Name: Alan Madewell, P.E.

Title: Manager, Environmental, Energy Supp

Company: Progress Energy Carolinas, Inc.

Sign Date: 9/3/2010

Name: Carl Vineyard, P.E.

Title: Project Manager

Company: Grace Consulting, Inc.

Sign Date: 9/3/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Progress Energy, Weatherspoon, Unit 1

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 17, 2011 Page 1 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Facility Information:

NCPEC

410 S. Wilmington Street

PEB 4A

Raleigh NC 27601

Contact: Cynthia Winston

Phone: 919-546-5538

Fax: 919-546-6302

Email: Cynthia.Winston@pgnmail.com

Testing Company:

Grace Consulting, Inc.

510 Dickson Street

Wellington OH 44090

Contact:Carl Vineyard

Phone: 440-647-6672

Fax: 440-647-6673

Email: carlvineyard@gcitest.com

Air Permit Number:

06094T15

Permitted Source ID/Name:

Unit 1 Boiler Weatherspoon

Permitted Maximum Process Rate:

655 mmBtu/hr

Max. Normal Operation Process Rate:

1324 mmBtu/hr

Target Process Test Rate

Normal Load

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Coal Fired Boiler with electrostatic precipitators.

Industry/SCC/NAIS 4911

Sampling Location Information:

Test Parameter Information:

AFS #: 371550047 FRS #: 110000550049

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Unit 1 Stack 150 0 0 0 1134 722 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Unit 1 Stack Carbon Monoxide Method 10 3 120 0

Unit 1 Stack Formaldehyde Method 0011 3 120 0

Total organic compounds 

(TOC) as Propane

Unit 1 Stack Method 25A 3 120 0

Unit 1 Stack Hydrogen Chloride Method 26A 3 180 0

Unit 1 Stack Hydrogen Fluoride Method 26A 3 180 0

Unit 1 Stack Filterable PM2.5 OTM - 27/28 3 360 0

Unit 1 Stack Total Particulate OTM - 27/28 3 360 0

Thursday, February 17, 2011 Page 2 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

The HCN was sampled using CTM 033 with 6N NaOH and an additional impinger for one hur per the clarification 

given by the USEPA in FAQ #10.

Unit 1 Stack Filterable Particulate OTM - 27/28 3 360 0

Organic Condensible 

Particulate

Unit 1 Stack OTM - 27/28 3 360 0

Inorganic (Aqueous) 

Condensible Part.

Unit 1 Stack OTM - 27/28 3 360 0

Unit 1 Stack Total PM2.5 OTM - 27/28 3 360 0

Unit 1 Stack Beryllium Method 29 3 240 0

Unit 1 Stack Cadmium Method 29 3 240 0

Unit 1 Stack Chromium Method 29 3 240 0

Unit 1 Stack Manganese Method 29 3 240 0

Unit 1 Stack Nickel Method 29 3 240 0

Unit 1 Stack Antimony Method 29 3 240 0

Unit 1 Stack Cobalt Method 29 3 240 0

Unit 1 Stack Selenium Method 29 3 240 0

Unit 1 Stack Lead Method 29 3 240 0

Unit 1 Stack Arsenic Method 29 3 240 0

Unit 1 Stack Co2 Method 3A CO2 9 120 0

Unit 1 Stack O2 Method 3A O2 9 120 0

Unit 1 Stack Sulfur Dioxide Method 6C 3 180 0

Unit 1 Stack Nitrogen oxides (NOx) Method 7E 3 180 0

Thursday, February 17, 2011 Page 3 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Sampling / Stack Data Results Summary

Location Unit 1 Stack - Method 0011

Average

Run Number 1 2 3

Test Date 2/17/2010 2/18/2010 2/18/2010

Run Start Time 4:20:00 PM 8:00:00 

AM

10:50:00 AM

Run Finish Time 6:15:00 PM 9:55:00 

AM

12:45:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 95.357 97.307 97.059 96.574

Moisture Content of Stack Gas, % 5.03 4.89 4.95 4.957

Moisture Saturation at Stack Gas Temperature, % 100.00 96.40 100.00 98.800

Carbon Dioxide, % 9.2 9.4 9.8 9.467

Oxygen, % 10.3 10.3 10 10.200

Average Stack Gas Temperature, °F 223.08 210.00 222.50 218.527

Dry Volumetric Flow Rate, dry scfm 184,876.8 188,882.3 187,950.0 187,236.367

Actual Wet Volumetric Flue Gas Flow Rate, acfm 252,774.5 252,848.2 256,456.1 254,026.267

Percent Isokinetic of Sampling Rate, % 98.7 98.6 98.8 98.700

F-Factor, dscfm/MMBtu @ %O2 9629 9407 9407 9,481.000

Fw

Fc

Location Unit 1 Stack - Method 10

Average

Run Number 1 2 3

Test Date 2/17/2010 2/18/2010 2/18/2010

Run Start Time 4:20:00 PM 8:00:00 

AM

10:50:00 AM

Run Finish Time 6:29:00 PM 10:10:00 

AM

1:02:00 PM

Carbon Dioxide, % 9.2 9.4 9.8 9.467

Oxygen, % 10.3 10.3 10 10.200

Dry Volumetric Flow Rate, dry scfm 194340 198451 197865 196,885.333

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 4.6 4.9 4.9 4.800

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Thursday, February 17, 2011 Page 4 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 25A

Average

Run Number 1 2 3

Test Date 2/17/2010 2/18/2010 2/18/2010

Run Start Time 4:20:00 PM 8:00:00 

AM

10:50:00 AM

Run Finish Time 6:29:00 PM 10:10:00 

AM

1:00:00 PM

Carbon Dioxide, % 9.2 9.4 9.8 9.467

Oxygen, % 10.3 10.3 10 10.200

Dry Volumetric Flow Rate, dry scfm 194340 198451 197865 196,885.333

F-Factor, dscfm/MMBtu @ %O2 9629 9322 9687 9,546.000

Moisture, % 4.6 4.9 4.9 4.800

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Location Unit 1 Stack - Method 26A

Average

Run Number 1 2 3

Test Date 2/19/2010 2/19/2010 2/19/2010

Run Start Time 8:45:00 AM 12:05:00 

PM

3:30:00 PM

Run Finish Time 11:37:30 AM 2:57:30 PM 6:22:30 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 143.350 139.497 141.137 141.328

Moisture Content of Stack Gas, % 4.13 4.86 4.34 4.443

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 9.9 10 9.3 9.733

Oxygen, % 9.8 9.5 10.3 9.867

Average Stack Gas Temperature, °F 229.96 242.42 249.33 240.570

Dry Volumetric Flow Rate, dry scfm 185,094.9 180,163.6 181,745.3 182,334.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 252,038.2 251,670.1 254,983.5 252,897.267

Percent Isokinetic of Sampling Rate, % 98.2 98.2 98.5 98.300

F-Factor, dscfm/MMBtu @ %O2 9184 9690 9494 9,456.000

Fw

Fc

Thursday, February 17, 2011 Page 5 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 29

Average

Run Number 1 2 3

Test Date 2/16/2010 2/16/2010 2/17/2010

Run Start Time 9:45:00 AM 5:30:00 PM 8:05:00 AM

Run Finish Time 1:40:00 PM 8:44:00 PM 1:00:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 155.253 156.628 158.177 156.686

Moisture Content of Stack Gas, % 4.87 4.59 8.49 5.983

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 8.8 9 9.2 9.000

Oxygen, % 10.7 10.6 10.5 10.600

Average Stack Gas Temperature, °F 221.83 213.19 215.81 216.943

Dry Volumetric Flow Rate, dry scfm 184,197.1 189,243.4 184,673.2 186,037.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 251,891.0 254,762.6 259,254.0 255,302.533

Percent Isokinetic of Sampling Rate, % 100.1 98.3 101.7 100.033

F-Factor, dscfm/MMBtu @ %O2 9459 9684 9629 9,590.667

Fw

Fc

Location Unit 1 Stack - Method 3A CO2

Average

Run Number 1 1A 1B

Test Date 2/17/2010 2/19/2010 2/16/2010

Run Start Time 4:20:00 PM 8:45:00 

AM

9:45:00 AM

Run Finish Time 6:29:00 PM 11:53:00 

AM

4:14:00 PM

Carbon Dioxide, % 9.2 9.9 8.8 9.300

Oxygen, % 10.3 9.8 10.7 10.267

Dry Volumetric Flow Rate, dry scfm 194340 196035 207408 199,261.000

F-Factor, dscfm/MMBtu @ %O2 9629 9184 9459 9,424.000

Moisture, % 4.6 5.7 5.9 5.400

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Thursday, February 17, 2011 Page 6 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A CO2 3

Average

Run Number 2 2A 2B

Test Date 2/18/2010 2/19/2010 2/16/2010

Run Start Time 8:00:00 AM 12:05:00 

PM

5:30:00 PM

Run Finish Time 10:10:00 AM 3:13:00 PM 11:48:00 PM

Carbon Dioxide, % 9.4 10 9 9.467

Oxygen, % 10.3 9.5 10.6 10.133

Dry Volumetric Flow Rate, dry scfm 198451 191195 210288 199,978.000

F-Factor, dscfm/MMBtu @ %O2 9322 9690 9684 9,565.333

Moisture, % 4.9 6.4 6.3 5.867

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Location Unit 1 Stack - Method 3A CO2 3 6

Average

Run Number 3 3A 3B

Test Date 2/18/2010 2/19/2010 2/17/2010

Run Start Time 10:50:00 AM 3:30:00 PM 8:05:00 AM

Run Finish Time 1:02:00 PM 7:15:00 PM 2:40:00 PM

Carbon Dioxide, % 9.8 9.3 9.2 9.433

Oxygen, % 10 10.3 10.5 10.267

Dry Volumetric Flow Rate, dry scfm 197865 191877 208109 199,283.667

F-Factor, dscfm/MMBtu @ %O2 9322 9494 9629 9,481.667

Moisture, % 4.9 6.1 5.8 5.600

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Thursday, February 17, 2011 Page 7 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A O2

Average

Run Number 1 1A 1B

Test Date 2/17/2010 2/19/2010 2/16/2010

Run Start Time 4:20:00 PM 8:45:00 

AM

9:45:00 AM

Run Finish Time 6:29:00 PM 11:53:00 

AM

4:14:00 PM

Carbon Dioxide, % 9.2 9.9 8.8 9.300

Oxygen, % 10.3 9.8 10.7 10.267

Dry Volumetric Flow Rate, dry scfm 194340 196035 207408 199,261.000

F-Factor, dscfm/MMBtu @ %O2 9629 9184 9459 9,424.000

Moisture, % 4.6 5.7 5.9 5.400

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Location Unit 1 Stack - Method 3A O2 3

Average

Run Number 2 2A 2B

Test Date 2/18/2010 2/19/2010 2/16/2010

Run Start Time 8:00:00 AM 12:05:00 

PM

5:30:00 PM

Run Finish Time 10:10:00 AM 3:13:00 PM 11:48:00 PM

Carbon Dioxide, % 9.4 10 9 9.467

Oxygen, % 10.3 9.5 10.6 10.133

Dry Volumetric Flow Rate, dry scfm 198451 191195 210288 199,978.000

F-Factor, dscfm/MMBtu @ %O2 9322 9690 9684 9,565.333

Moisture, % 4.9 6.4 6.3 5.867

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Thursday, February 17, 2011 Page 8 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A O2 3 6

Average

Run Number 3 3A 3B

Test Date 2/18/2010 2/19/2010 2/17/2010

Run Start Time 10:50:00 AM 3:30:00 PM 8:05:00 AM

Run Finish Time 1:02:00 PM 7:15:00 PM 2:40:00 PM

Carbon Dioxide, % 9.8 9.3 9.2 9.433

Oxygen, % 10 10.3 10.5 10.267

Dry Volumetric Flow Rate, dry scfm 197865 197877 208109 201,283.667

F-Factor, dscfm/MMBtu @ %O2 9322 9494 9629 9,481.667

Moisture, % 4.9 6.1 5.8 5.600

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Location Unit 1 Stack - Method 6C

Average

Run Number 1 2 3

Test Date 2/19/2010 2/19/2010 2/19/2010

Run Start Time 8:45:00 AM 12:05:00 

PM

3:30:00 PM

Run Finish Time 11:53:00 AM 3:13:00 PM 7:15:00 PM

Carbon Dioxide, % 9.9 10 9.3 9.733

Oxygen, % 9.8 9.5 10.3 9.867

Dry Volumetric Flow Rate, dry scfm 196035 191195 191877 193,035.667

F-Factor, dscfm/MMBtu @ %O2 9184 9690 9494 9,456.000

Moisture, % 5.7 6.4 6.1 6.067

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Thursday, February 17, 2011 Page 9 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 7E

Average

Run Number 1 2 3

Test Date 2/19/2010 2/19/2010 2/19/2010

Run Start Time 8:45:00 AM 12:05:00 

PM

3:30:00 PM

Run Finish Time 11:53:00 AM 3:13:00 PM 7:15:00 PM

Carbon Dioxide, % 9.9 10 9.3 9.733

Oxygen, % 9.8 9.5 10.3 9.867

Dry Volumetric Flow Rate, dry scfm 196035 191195 191877 193,035.667

F-Factor, dscfm/MMBtu @ %O2 9184 9690 9494 9,456.000

Moisture, % 5.7 6.4 6.1 6.067

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Location Unit 1 Stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 2/16/2010 2/16/2010 2/17/2010

Run Start Time 9:45:00 AM 5:30:00 PM 8:05:00 AM

Run Finish Time 3:35:00 PM 11:20:00 

PM

1:55:00 PM

Net Run Time, minutes 365.9 366.6 358.8

Dry Gas Meter Volume Sampled, dscf 132.562 134.621 133.967 133.717

Moisture Content of Stack Gas, % 5.55 6.32 5.80 5.890

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 8.8 9 9.2 9.000

Oxygen, % 10.7 10.6 10.5 10.600

Average Stack Gas Temperature, °F 222.03 217.58 220.50 220.037

Dry Volumetric Flow Rate, dry scfm 195,759.9 197,199.8 196,137.3 196,365.667

Actual Wet Volumetric Flue Gas Flow Rate, acfm 269,709.6 272,139.4 269,341.5 270,396.833

Percent Isokinetic of Sampling Rate, % 89.2 89.8 91.8 90.267

F-Factor, dscfm/MMBtu @ %O2 9459 9684 9629 9,590.667

Fw

Fc

Thursday, February 17, 2011 Page 10 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Emissions Summary

Location: Unit 1 Stack - Method 0011

Compound: Formaldehyde

Average

RunNumber 1 2 3

Mass_mg 0.102 0.0833 0.071 0.085

Elb/hr 2.62E-02 2.14E-02 1.82E-02 0.022

gr/dscf 1.65E-05 1.32E-05 1.13E-05 0.000

lb/mmBtuO2 4.48E-05 3.50E-05 2.91E-05 0.000

ppm 3.03E-02 2.42E-02 2.07E-02 0.025

ppm@7%O2 3.97E-02 3.17E-02 2.64E-02 0.033

Location: Unit 1 Stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 1.55E-02 1.37E-02 9.96E-03 0.013

ppm 1.11E+01 9.78E+00 7.31E+00 9.397

ppm@7%O2 1.46E+01 1.28E+01 9.32E+00 12.240

Location: Unit 1 Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 3.30E-05 3.70E-04 3.11E-04 0.000

ppm 1.52E-02 1.76E-01 1.46E-01 0.112

ppm@7%O2 1.99E-02 2.31E-01 1.86E-01 0.146

Location: Unit 1 Stack - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 342 355 338 345.000

lb/mmBtuO2 9.10E-02 9.97E-02 9.88E-02 0.097

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 26.1 30.4 25.2 27.233

lb/mmBtuO2 6.94E-03 8.54E-03 7.37E-03 0.008

Location: Unit 1 Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.002 0.002 0.002 0.002

lb/mmBtuO2 5.50E-07 5.53E-07 5.39E-07 0.000

Compound: Arsenic

Average

Thursday, February 17, 2011 Page 11 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

RunNumber 1 2 3

Mass_mg 0.0093 0.0143 0.0195 0.014

lb/mmBtuO2 2.56E-06 3.96E-06 5.26E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00009 0.00023 0.00073 0.000

lb/mmBtuO2 2.48E-08 6.36E-08 1.97E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00029 0.00025 0.00033 0.000

lb/mmBtuO2 7.98E-08 6.91E-08 8.90E-08 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0127 0.0297 0.0215 0.021

lb/mmBtuO2 3.50E-06 8.21E-06 5.80E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.0039 0.0028 0.0032 0.003

lb/mmBtuO2 1.07E-06 7.74E-07 8.63E-07 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0026 0.0044 0.0074 0.005

lb/mmBtuO2 7.16E-07 1.22E-06 2.00E-06 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0462 0.0022 0.0944 0.048

lb/mmBtuO2 1.27E-05 6.08E-07 2.55E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0186 0.0207 0.0189 0.019

lb/mmBtuO2 5.12E-06 5.73E-06 5.10E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.3182 0.2619 0.1207 0.234

lb/mmBtuO2 8.76E-05 7.24E-05 3.26E-05 0.000

Location: Unit 1 Stack - Method 6C

Thursday, February 17, 2011 Page 12 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 1.53E+00 1.63E+00 1.65E+00 1.603

ppm 5.33E+02 5.53E+02 5.31E+02 539.000

ppm@7%O2 6.67E+02 6.74E+02 6.96E+02 679.000

Location: Unit 1 Stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 7.64E-01 8.43E-01 8.12E-01 0.806

ppm 3.70E+02 3.97E+02 3.63E+02 376.667

ppm@7%O2 4.63E+02 4.84E+02 4.76E+02 474.333

Location: Unit 1 Stack - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 16.2 236.3 124.3 125.600

Elb/hr 3.16E+00 4.58E+01 2.41E+01 24.353

lb/mmBtuO2 5.22E-03 7.60E-02 3.96E-02 0.040

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 5 13.6 41.5 20.033

Elb/hr 9.77E-01 2.64E+00 8.04E+00 3.886

lb/mmBtuO2 1.61E-03 4.38E-03 1.32E-02 0.006

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 308 209 22.8 179.933

Elb/hr 6.02E+01 4.05E+01 4.42E+00 35.040

lb/mmBtuO2 9.93E-02 6.73E-02 7.26E-03 0.058

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 13.4 5.2 18.8 12.467

Elb/hr 2.62E+00 1.01E+00 3.64E+00 2.423

lb/mmBtuO2 4.32E-03 1.67E-03 5.99E-03 0.004

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 337.6 450.5 165.9 318.000

Elb/hr 6.59E+01 8.73E+01 3.21E+01 61.767

lb/mmBtuO2 1.09E-01 1.45E-01 5.28E-02 0.102

Thursday, February 17, 2011 Page 13 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Process Run Data

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 326.4 227.8 83.1 212.433

Elb/hr 6.38E+01 4.41E+01 1.61E+01 41.333

lb/mmBtuO2 1.05E-01 7.33E-02 2.65E-02 0.068

Thursday, February 17, 2011 Page 14 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 397.3 300

1 Steam Output 4600001000 lb steam/hr 460000

1 Gross Electrical Output 960 MW 900

1 Net Electrical Output 874 MW 800

2 Heat Input Million Btus/million BTU using O2 425 300

2 Steam Output 4600001000 lb steam/hr 460000

2 Gross Electrical Output 1042 MW 900

2 Net Electrical Output 955 MW 800

3 Heat Input Million Btus/million BTU using O2 385 300

3 Steam Output 4600001000 lb steam/hr 460000

3 Gross Electrical Output 929 MW 900

3 Net Electrical Output 846 MW 800

Run Name Value UOM Comments

Target

Value

1 ELECTROSTATIC PRECIPITATOR 0 0

Run Name Value UOM Comments

1 0

Thursday, February 17, 2011 Page 15 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Sampling / Stack Data Results Detail

Location Unit 1 Stack - Method 0011

Average

Run Number 1 2 3

Test Date 2/17/2010 2/18/2010 2/18/2010

Run Start Time 4:20:00 PM 8:00:00 AM 10:50:00 AM

Run Finish Time 6:15:00 PM 9:55:00 AM 12:45:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.313 0.313 0.313 0.313

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.016 1.016 1.016 1.016

Barometric Pressure, inches of Mercury 29.85 29.86 29.86 29.857

Average Orifice Meter Differential, inches H2O 1.77 1.74 1.77 1.760

Dry Gas Meter Volume Sampled, cubic feet 91.968 91.048 91.847 91.621

Average Dry Gas Meter Temperature, °F 58.42 43.08 48.83 50.110

Dry Gas Meter Volume Sampled, dscf 95.357 97.307 97.059 96.574

Total Moisture Liquid collected, g 107.2 106.2 107.2 106.867

Volume of Water Vapor, standard cubic feet 5.05 5.00 5.05 5.033

Moisture Content of Stack Gas, % 5.03 4.89 4.95 4.957

Moisture Saturation at Stack Gas Temperature, % 100.00 96.40 100.00 98.800

Dry Mole Fraction 0.9497 0.9511 0.9505 0.950

Carbon Dioxide, % 9.2 9.4 9.8 9.467

Oxygen, % 10.3 10.3 10 10.200

Carbon Monoxide & Nitrogen, % 80.5 80.3 80.2 80.333

Fuel Factor 1.15 1.13 1.11

Dry Molecular Weight, lb/lb-Mole 29.88 29.92 29.97 29.923

Wet Molecular weight, lb/lb-Mole 29.28 29.34 29.38 29.333

Flue Gas Static Pressure, inches of H2O -0.55 -0.55 -0.61 -0.570

Absolute Flue Gas Pressure, inches of Mercury 29.81 29.82 29.82 29.817

Average Stack Gas Temperature, °F 223.08 210.00 222.50 218.527

Average Velocity Head, inches of H2O 0.2919758976

34987

0.298641816

133831

0.301979476

604218

0.298

Average Stack Gas Velocity, feet/second 34.33 34.34 34.83 34.500

Stack Cross-Sectional Area, square feet 122.718 122.718 122.718 122.718

Dry Volumetric Flow Rate, dry scfm 184,876.8 188,882.3 187,950.0 187,236.367

Actual Wet Volumetric Flue Gas Flow Rate, acfm 252,774.5 252,848.2 256,456.1 254,026.267

Percent Isokinetic of Sampling Rate, % 98.7 98.6 98.8 98.700

Percent Excess Air, % 94.0 94.5 89.5 92.667

F-Factor, dscfm/MMBtu @ %O2 9629 9407 9407 9,481.000

Round Duct Diameter, inches 150 150 150

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Thursday, February 17, 2011 Page 16 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 10

Average

Run Number 1 2 3

Test Date 2/17/2010 2/18/2010 2/18/2010

Run Start Time 4:20:00 PM 8:00:00 AM 10:50:00 AM

Run Finish Time 6:29:00 PM 10:10:00 AM 1:02:00 PM

Carbon Dioxide, % 9.2 9.4 9.8 9.467

Oxygen, % 10.3 10.3 10 10.200

Fuel Factor 1.15 1.13 1.11

Dry Volumetric Flow Rate, dry scfm 194340 198451 197865 196,885.333

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 4.6 4.9 4.9 4.800

Analyzer Make Horiba Horiba Horiba

Analyzer Model VIA-510 VIA-510 VIA-510

Analyzer Serial Number 570124044 570124044 570124044 570,124,044

.000

Operating Range 27.9 27.9 27.9 27.900

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 18 19 19 18.667

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.15 0.18 0.12 0.150

Calibration Pre Zero Cylinder Bias -0.11 0.14 -0.07 -0.013

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0000935 EB0000935 EB0000935

Calibration Pre High Cylinder Instrument Response 15.99 15.99 16.08 16.020

Calibration Pre High Cylinder Bias 0.11 0 0.32 0.143

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.14 0.12 0.13 0.130

Calibration Post Zero Cylinder Bias -0.14 -0.07 -0.04 -0.083

Calibration Post Zero Cylinder Drift 0.03 0.21 0.03 0.090

Calibration Post High Cylinder ID EB0000935 EB0000935 EB0000935

Calibration Post High Cylinder Instrument Response 15.87 16.08 16.01 15.987

Calibration Post High Cylinder Bias -0.32 0.32 0.07 0.023

Calibration Post High Cylinder Drift 0.43 0.32 0.25 0.333

Cavg 11.12 9.92 7.44 9.493

Cavg Units ppmvd ppmvd ppmvd

Cgas 11.055 9.7792 7.3058 9.380

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 17 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 25A

Average

Run Number 1 2 3

Test Date 2/17/2010 2/18/2010 2/18/2010

Run Start Time 4:20:00 PM 8:00:00 AM 10:50:00 AM

Run Finish Time 6:29:00 PM 10:10:00 AM 1:00:00 PM

Carbon Dioxide, % 9.2 9.4 9.8 9.467

Oxygen, % 10.3 10.3 10 10.200

Fuel Factor 1.15 1.13 1.11

Dry Volumetric Flow Rate, dry scfm 194340 198451 197865 196,885.333

F-Factor, dscfm/MMBtu @ %O2 9629 9322 9687 9,546.000

Moisture, % 4.6 4.9 4.9 4.800

Analyzer Make Thermo 

Environmental

Thermo 

Environment

al

Thermo 

Environmenta

l

Analyzer Model Model 51 Model 51 51

Analyzer Serial Number 4723 4723 4723 4,723.000

Operating Range 46.9 46.9 46.9 46.900

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 1 2 2 1.667

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.2 0.15 0.1 0.150

Calibration Pre Zero Cylinder Bias 0.02 0.11 0 0.043

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0002605 EB0002605 EB0002605

Calibration Pre High Cylinder Instrument Response 25.81 26.24 26.01 26.020

Calibration Pre High Cylinder Bias -1.09 0.19 -0.3 -0.400

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.17 0.1 0.13 0.133

Calibration Post Zero Cylinder Bias -0.04 0 0.06 0.007

Calibration Post Zero Cylinder Drift 0.06 0.11 0.06 0.077

Calibration Post High Cylinder ID EB0002605 EB0002605 EB0002605

Calibration Post High Cylinder Instrument Response 25.94 26.01 25.95 25.967

Calibration Post High Cylinder Bias -0.81 -0.3 -0.43 -0.513

Calibration Post High Cylinder Drift 0.81 0.49 0.13 0.477

Cavg 0.2 0.3 0.26 0.253

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.0152 0.1757 0.1463 0.112

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units ppmvw

Thursday, February 17, 2011 Page 18 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 26A

Average

Run Number 1 2 3

Test Date 2/19/2010 2/19/2010 2/19/2010

Run Start Time 8:45:00 AM 12:05:00 PM 3:30:00 PM

Run Finish Time 11:37:30 AM 2:57:30 PM 6:22:30 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.314 0.314 0.314 0.314

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.016 1.016 1.016 1.016

Barometric Pressure, inches of Mercury 29.99 29.99 29.99 29.990

Average Orifice Meter Differential, inches H2O 1.81 1.84 1.91 1.853

Dry Gas Meter Volume Sampled, cubic feet 134.944 134.944 138.903 136.264

Average Dry Gas Meter Temperature, °F 48.42 62.50 71.67 60.863

Dry Gas Meter Volume Sampled, dscf 143.350 139.497 141.137 141.328

Total Moisture Liquid collected, g 131 151.2 136.2 139.467

Volume of Water Vapor, standard cubic feet 6.17 7.12 6.41 6.567

Moisture Content of Stack Gas, % 4.13 4.86 4.34 4.443

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9587 0.9514 0.9566 0.956

Carbon Dioxide, % 9.9 10 9.3 9.733

Oxygen, % 9.8 9.5 10.3 9.867

Carbon Monoxide & Nitrogen, % 80.3 80.5 80.4 80.400

Fuel Factor 1.12 1.14 1.14

Dry Molecular Weight, lb/lb-Mole 29.98 29.98 29.90 29.953

Wet Molecular weight, lb/lb-Mole 29.49 29.40 29.38 29.423

Flue Gas Static Pressure, inches of H2O -0.55 -0.55 -0.61 -0.570

Absolute Flue Gas Pressure, inches of Mercury 29.95 29.95 29.95 29.950

Average Stack Gas Temperature, °F 229.96 242.42 249.33 240.570

Average Velocity Head, inches of H2O 0.2908057090

56929

0.283955543

693885

0.288453321

943969

0.288

Average Stack Gas Velocity, feet/second 34.23 34.18 34.63 34.347

Stack Cross-Sectional Area, square feet 122.718 122.718 122.718 122.718

Dry Volumetric Flow Rate, dry scfm 185,094.9 180,163.6 181,745.3 182,334.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 252,038.2 251,670.1 254,983.5 252,897.267

Percent Isokinetic of Sampling Rate, % 98.2 98.2 98.5 98.300

Percent Excess Air, % 86.0 80.8 94.3 87.033

F-Factor, dscfm/MMBtu @ %O2 9184 9690 9494 9,456.000

Round Duct Diameter, inches 150 150 150

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Thursday, February 17, 2011 Page 19 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 29

Average

Run Number 1 2 3

Test Date 2/16/2010 2/16/2010 2/17/2010

Run Start Time 9:45:00 AM 5:30:00 PM 8:05:00 AM

Run Finish Time 1:40:00 PM 8:44:00 PM 1:00:00 PM

Net Traversing Points 25 25 25

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.281 0.281 0.281 0.281

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.016 1.016 1.016 1.016

Barometric Pressure, inches of Mercury 29.74 29.74 29.85 29.777

Average Orifice Meter Differential, inches H2O 1.19 1.26 1.25 1.233

Dry Gas Meter Volume Sampled, cubic feet 147.929 150.112 149.323 149.121

Average Dry Gas Meter Temperature, °F 49.56 52.63 46.79 49.660

Dry Gas Meter Volume Sampled, dscf 155.253 156.628 158.177 156.686

Total Moisture Liquid collected, g 168.8 160.2 311.6 213.533

Volume of Water Vapor, standard cubic feet 7.95 7.54 14.67 10.053

Moisture Content of Stack Gas, % 4.87 4.59 8.49 5.983

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9513 0.9541 0.9151 0.940

Carbon Dioxide, % 8.8 9 9.2 9.000

Oxygen, % 10.7 10.6 10.5 10.600

Carbon Monoxide & Nitrogen, % 80.5 80.4 80.3 80.400

Fuel Factor 1.16 1.14 1.13

Dry Molecular Weight, lb/lb-Mole 29.84 29.86 29.89 29.863

Wet Molecular weight, lb/lb-Mole 29.26 29.32 28.88 29.153

Flue Gas Static Pressure, inches of H2O -0.55 -0.55 -0.61 -0.570

Absolute Flue Gas Pressure, inches of Mercury 29.70 29.70 29.81 29.737

Average Stack Gas Temperature, °F 221.83 213.19 215.81 216.943

Average Velocity Head, inches of H2O 0.2892753832

07848

0.300355397

509486

0.306333843

162029

0.299

Average Stack Gas Velocity, feet/second 34.21 34.60 35.21 34.673

Stack Cross-Sectional Area, square feet 122.718 122.718 122.718 122.718

Dry Volumetric Flow Rate, dry scfm 184,197.1 189,243.4 184,673.2 186,037.900

Actual Wet Volumetric Flue Gas Flow Rate, acfm 251,891.0 254,762.6 259,254.0 255,302.533

Percent Isokinetic of Sampling Rate, % 100.1 98.3 101.7 100.033

Percent Excess Air, % 101.4 99.8 98.1 99.767

F-Factor, dscfm/MMBtu @ %O2 9459 9684 9629 9,590.667

Round Duct Diameter, inches 150 150 150

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Thursday, February 17, 2011 Page 20 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A CO2

Average

Run Number 1 1A 1B

Test Date 2/17/2010 2/19/2010 2/16/2010

Run Start Time 4:20:00 PM 8:45:00 AM 9:45:00 AM

Run Finish Time 6:29:00 PM 11:53:00 AM 4:14:00 PM

Carbon Dioxide, % 9.2 9.9 8.8 9.300

Oxygen, % 10.3 9.8 10.7 10.267

Fuel Factor 1.15 1.12 1.16

Dry Volumetric Flow Rate, dry scfm 194340 196035 207408 199,261.000

F-Factor, dscfm/MMBtu @ %O2 9629 9184 9459 9,424.000

Moisture, % 4.6 5.7 5.9 5.400

Analyzer Make Calif. 

Analytical

Calif 

Analytical

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 18 18 18 18.000

Operating Units % % %

No. Readings/Avg. 120 180 360 220.000

Calibration Set 5 14 9 9.333

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.12 0.18 0.12 0.140

Calibration Pre Zero Cylinder Bias 0 0.17 -0.11 0.020

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275960 CC275960 CC275960

Calibration Pre High Cylinder Instrument Response 9.07 8.96 9.07 9.033

Calibration Pre High Cylinder Bias 0.94 -0.17 0.44 0.403

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.11 0.22 0.11 0.147

Calibration Post Zero Cylinder Bias -0.06 0.39 -0.17 0.053

Calibration Post Zero Cylinder Drift 0.06 0.22 0.06 0.113

Calibration Post High Cylinder ID CC275960 CC275960 CC275960

Calibration Post High Cylinder Instrument Response 9 8.9 9 8.967

Calibration Post High Cylinder Bias 0.56 -0.5 0.06 0.040

Calibration Post High Cylinder Drift 0.38 0.33 0.38 0.363

Cavg 9.28 9.89 8.87 9.347

Cavg Units %vd %vd %vd

Cgas 9.2061 9.9453 8.7943 9.315

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units %vw

Thursday, February 17, 2011 Page 21 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A CO2 3

Average

Run Number 2 2A 2B

Test Date 2/18/2010 2/19/2010 2/16/2010

Run Start Time 8:00:00 AM 12:05:00 PM 5:30:00 PM

Run Finish Time 10:10:00 AM 3:13:00 PM 11:48:00 PM

Carbon Dioxide, % 9.4 10 9 9.467

Oxygen, % 10.3 9.5 10.6 10.133

Fuel Factor 1.13 1.14 1.14

Dry Volumetric Flow Rate, dry scfm 198451 191195 210288 199,978.000

F-Factor, dscfm/MMBtu @ %O2 9322 9690 9684 9,565.333

Moisture, % 4.9 6.4 6.3 5.867

Analyzer Make Calif. 

Analytical

Calif 

Analytical

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 18 18 18 18.000

Operating Units % % %

No. Readings/Avg. 120 180 360 220.000

Calibration Set 6 14 9 9.667

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.15 0.22 0.11 0.160

Calibration Pre Zero Cylinder Bias 0 0.39 -0.17 0.073

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275960 CC275960 CC275960

Calibration Pre High Cylinder Instrument Response 8.99 8.9 9 8.963

Calibration Pre High Cylinder Bias -49.83 -0.5 0.06 -16.757

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.1 0.29 0.1 0.163

Calibration Post Zero Cylinder Bias -0.28 0.78 -0.22 0.093

Calibration Post Zero Cylinder Drift 0.28 0.39 0.05 0.240

Calibration Post High Cylinder ID CC275960 CC275960 CC275960

Calibration Post High Cylinder Instrument Response 8.93 8.97 9.01 8.970

Calibration Post High Cylinder Bias -0.33 -0.11 0.11 -0.110

Calibration Post High Cylinder Drift 49.5 0.39 0.05 16.647

Cavg 9.41 9.91 9.06 9.460

Cavg Units %vd %vd %vd

Cgas 9.4164 9.9665 9.0154 9.466

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 22 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A CO2 3 6

Average

Run Number 3 3A 3B

Test Date 2/18/2010 2/19/2010 2/17/2010

Run Start Time 10:50:00 AM 3:30:00 PM 8:05:00 AM

Run Finish Time 1:02:00 PM 7:15:00 PM 2:40:00 PM

Carbon Dioxide, % 9.8 9.3 9.2 9.433

Oxygen, % 10 10.3 10.5 10.267

Fuel Factor 1.11 1.14 1.13

Dry Volumetric Flow Rate, dry scfm 197865 191877 208109 199,283.667

F-Factor, dscfm/MMBtu @ %O2 9322 9494 9629 9,481.667

Moisture, % 4.9 6.1 5.8 5.600

Analyzer Make Calif. 

Analytical

Calif 

Analyzer

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 18 18 18 18.000

Operating Units % % %

No. Readings/Avg. 120 180 360 220.000

Calibration Set 6 14 5 8.333

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.1 0.29 0.12 0.170

Calibration Pre Zero Cylinder Bias -0.28 0.78 -0.11 0.130

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC275960 CC275960 CC275960

Calibration Pre High Cylinder Instrument Response 8.93 8.97 8.96 8.953

Calibration Pre High Cylinder Bias -0.33 -0.11 -0.17 -0.203

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.1 0.2 0.05 0.117

Calibration Post Zero Cylinder Bias -0.28 0.28 -0.39 -0.130

Calibration Post Zero Cylinder Drift 0 0.5 0.28 0.260

Calibration Post High Cylinder ID CC275960 CC275960 CC275960

Calibration Post High Cylinder Instrument Response 8.99 9.05 9.05 9.030

Calibration Post High Cylinder Bias 0 0.33 0.83 0.387

Calibration Post High Cylinder Drift 0.33 0.44 1 0.590

Cavg 9.82 10.24 9.29 9.783

Cavg Units %vd ppmvd %vd

Cgas 9.8297 10.2174 9.2463 9.764

Cgas Units %vd ppmvd %vd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 23 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A O2

Average

Run Number 1 1A 1B

Test Date 2/17/2010 2/19/2010 2/16/2010

Run Start Time 4:20:00 PM 8:45:00 AM 9:45:00 AM

Run Finish Time 6:29:00 PM 11:53:00 AM 4:14:00 PM

Carbon Dioxide, % 9.2 9.9 8.8 9.300

Oxygen, % 10.3 9.8 10.7 10.267

Fuel Factor 1.15 1.12 1.16

Dry Volumetric Flow Rate, dry scfm 194340 196035 207408 199,261.000

F-Factor, dscfm/MMBtu @ %O2 9629 9184 9459 9,424.000

Moisture, % 4.6 5.7 5.9 5.400

Analyzer Make Calif. 

Analytical

Calif 

Analytical

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 22.4 22.4 22.4 22.400

Operating Units % % %

No. Readings/Avg. 120 180 360 220.000

Calibration Set 7 13 16 12.000

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.12 0.1 0.12 0.113

Calibration Pre Zero Cylinder Bias 0 0 -0.09 -0.030

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC2759601 CC2759601 CC2759601

Calibration Pre High Cylinder Instrument Response 11.01 10.87 11.01 10.963

Calibration Pre High Cylinder Bias 0.09 -0.27 -0.58 -0.253

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.15 0.16 0.15 0.153

Calibration Post Zero Cylinder Bias 0.13 0.27 0.04 0.147

Calibration Post Zero Cylinder Drift 0.13 0.27 0.13 0.177

Calibration Post High Cylinder ID CC2759601 CC2759601 CC2759601

Calibration Post High Cylinder Instrument Response 11.06 10.96 11.06 11.027

Calibration Post High Cylinder Bias 0.31 0.13 -0.36 0.027

Calibration Post High Cylinder Drift 0.22 0.4 0.22 0.280

Cavg 10.31 9.74 10.74 10.263

Cavg Units %vd %vd %vd

Cgas 10.2683 9.8016 10.7023 10.257

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 24 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A O2 3

Average

Run Number 2 2A 2B

Test Date 2/18/2010 2/19/2010 2/16/2010

Run Start Time 8:00:00 AM 12:05:00 PM 5:30:00 PM

Run Finish Time 10:10:00 AM 3:13:00 PM 11:48:00 PM

Carbon Dioxide, % 9.4 10 9 9.467

Oxygen, % 10.3 9.5 10.6 10.133

Fuel Factor 1.13 1.14 1.14

Dry Volumetric Flow Rate, dry scfm 198451 191195 210288 199,978.000

F-Factor, dscfm/MMBtu @ %O2 9322 9690 9684 9,565.333

Moisture, % 4.9 6.4 6.3 5.867

Analyzer Make Calif. 

Analytical

Calif 

Analytical

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 22.4 22.4 22.4 22.400

Operating Units % % %

No. Readings/Avg. 120 180 360 220.000

Calibration Set 8 13 16 12.333

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.13 0.16 0.15 0.147

Calibration Pre Zero Cylinder Bias -0.09 0.27 0.04 0.073

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC2759601 CC2759601 CC2759601

Calibration Pre High Cylinder Instrument Response 11 10.96 11.06 11.007

Calibration Pre High Cylinder Bias 0.13 0.13 -0.36 -0.033

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.12 0.18 0.1 0.133

Calibration Post Zero Cylinder Bias -0.13 0.36 -0.18 0.017

Calibration Post Zero Cylinder Drift 0.04 0.09 0.22 0.117

Calibration Post High Cylinder ID CC2759601 CC2759601 CC2759601

Calibration Post High Cylinder Instrument Response 11.01 10.9 11 10.970

Calibration Post High Cylinder Bias 0.18 -0.13 -0.63 -0.193

Calibration Post High Cylinder Drift 0.05 0.26 0.27 0.193

Cavg 10.27 9.49 10.66 10.140

Cavg Units %vd ppmvd %vd

Cgas 10.2569 9.5279 10.6268 10.137

Cgas Units %vd ppmvd %vd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 25 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 3A O2 3 6

Average

Run Number 3 3A 3B

Test Date 2/18/2010 2/19/2010 2/17/2010

Run Start Time 10:50:00 AM 3:30:00 PM 8:05:00 AM

Run Finish Time 1:02:00 PM 7:15:00 PM 2:40:00 PM

Carbon Dioxide, % 9.8 9.3 9.2 9.433

Oxygen, % 10 10.3 10.5 10.267

Fuel Factor 1.11 1.14 1.13

Dry Volumetric Flow Rate, dry scfm 197865 197877 208109 201,283.667

F-Factor, dscfm/MMBtu @ %O2 9322 9494 9629 9,481.667

Moisture, % 4.9 6.1 5.8 5.600

Analyzer Make Calif. 

Analytical

Calif 

Analytical

Calif 

Analytical

Analyzer Model 200 200 200 200.000

Analyzer Serial Number 1L05017 1L05017 1L05017

Operating Range 22.4 22.4 22.4 22.400

Operating Units % % %

No. Readings/Avg. 120 180 360 220.000

Calibration Set 8 13 7 9.333

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.12 0.18 0.14 0.147

Calibration Pre Zero Cylinder Bias -0.13 0.36 0.09 0.107

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC2759601 CC2759601 CC2759601

Calibration Pre High Cylinder Instrument Response 11.01 10.9 11.09 11.000

Calibration Pre High Cylinder Bias 0.18 -0.13 0.45 0.167

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.1 0.22 0.12 0.147

Calibration Post Zero Cylinder Bias -0.22 0.54 0 0.107

Calibration Post Zero Cylinder Drift 0.09 0.18 0.09 0.120

Calibration Post High Cylinder ID CC2759601 CC2759601 CC2759601

Calibration Post High Cylinder Instrument Response 10.95 11 11.07 11.007

Calibration Post High Cylinder Bias -0.09 0.31 0.36 0.193

Calibration Post High Cylinder Drift 0.27 0.44 0.09 0.267

Cavg 10.03 10.24 10.59 10.287

Cavg Units %vd ppmvd %vd

Cgas 10.0386 10.2735 10.5078 10.273

Cgas Units %vd ppmvd %vd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 26 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 6C

Average

Run Number 1 2 3

Test Date 2/19/2010 2/19/2010 2/19/2010

Run Start Time 8:45:00 AM 12:05:00 PM 3:30:00 PM

Run Finish Time 11:53:00 AM 3:13:00 PM 7:15:00 PM

Carbon Dioxide, % 9.9 10 9.3 9.733

Oxygen, % 9.8 9.5 10.3 9.867

Fuel Factor 1.12 1.14 1.14

Dry Volumetric Flow Rate, dry scfm 196035 191195 191877 193,035.667

F-Factor, dscfm/MMBtu @ %O2 9184 9690 9494 9,456.000

Moisture, % 5.7 6.4 6.1 6.067

Analyzer Make Western 

Research

Western 

Research

Western 

research

Analyzer Model 721M 721M 721M

Analyzer Serial Number 93-721M8062-693-721M8062-693-721M8062-6

Operating Range 901 901 901 901.000

Operating Units ppm ppm ppm

No. Readings/Avg. 180 180 180 180.000

Calibration Set 12 12 12 12.000

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.85 0.93 0.75 0.843

Calibration Pre Zero Cylinder Bias 0.04 0.05 0.03 0.040

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0019497 EB0019497 EB0019497

Calibration Pre High Cylinder Instrument Response 505.58 507.96 504.72 506.087

Calibration Pre High Cylinder Bias -0.16 0.11 -0.25 -0.100

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.93 0.75 1.1 0.927

Calibration Post Zero Cylinder Bias 0.05 0.03 0.07 0.050

Calibration Post Zero Cylinder Drift 0.01 0.02 0.04 0.023

Calibration Post High Cylinder ID EB0019497 EB0019497 EB0019497

Calibration Post High Cylinder Instrument Response 507.96 504.72 505.69 506.123

Calibration Post High Cylinder Bias 0.11 -0.25 -0.14 -0.093

Calibration Post High Cylinder Drift 0.27 0.36 0.11 0.247

Cavg 534.21 553.28 530.05 539.180

Cavg Units ppmvd ppmvd ppmvd

Cgas 533.4465 552.9864 530.9297 539.121

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 17, 2011 Page 27 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - Method 7E

Average

Run Number 1 2 3

Test Date 2/19/2010 2/19/2010 2/19/2010

Run Start Time 8:45:00 AM 12:05:00 PM 3:30:00 PM

Run Finish Time 11:53:00 AM 3:13:00 PM 7:15:00 PM

Carbon Dioxide, % 9.9 10 9.3 9.733

Oxygen, % 9.8 9.5 10.3 9.867

Fuel Factor 1.12 1.14 1.14

Dry Volumetric Flow Rate, dry scfm 196035 191195 191877 193,035.667

F-Factor, dscfm/MMBtu @ %O2 9184 9690 9494 9,456.000

Moisture, % 5.7 6.4 6.1 6.067

Analyzer Make Thermo 

Environmental

Thermo Thermo

Analyzer Model 42C 42C 42C

Analyzer Serial Number 67507-357 42CHL_675

07_357

42CHL_6750

7_357

Operating Range 491 491 491 491.000

Operating Units ppm ppm ppm

No. Readings/Avg. 180 180 180 180.000

Calibration Set 11 11 11 11.000

Calibration Pre Zero Cylinder ID 081409001 081409001 081409001

Calibration Pre Zero Cylinder Instrument Response 0.49 0.56 0.42 0.490

Calibration Pre Zero Cylinder Bias 0.03 0.05 0.02 0.033

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0003850 EB0003850 EB0003850

Calibration Pre High Cylinder Instrument Response 231.98 232.69 232.94 232.537

Calibration Pre High Cylinder Bias -0.12 0.03 0.08 -0.003

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID 081409001 081409001 081409001

Calibration Post Zero Cylinder Instrument Response 0.56 0.42 0.68 0.553

Calibration Post Zero Cylinder Bias 0.05 0.02 0.07 0.047

Calibration Post Zero Cylinder Drift 0.02 0.03 0.05 0.033

Calibration Post High Cylinder ID EB0003850 EB0003850 EB0003850

Calibration Post High Cylinder Instrument Response 232.69 232.94 232.41 232.680

Calibration Post High Cylinder Bias 0.03 0.08 -0.03 0.027

Calibration Post High Cylinder Drift 0.15 0.05 0.11 0.103

Cavg 370.2 398.5 364.01 377.570

Cavg Units ppmvd ppmvd ppmvd

Cgas 369.978 397.4532 363.2643 376.899

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units ug/wscm

Thursday, February 17, 2011 Page 28 of 29
Progress Energy, Weatherspoon, Unit 1

9/3/2010

Location Unit 1 Stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 2/16/2010 2/16/2010 2/17/2010

Run Start Time 9:45:00 AM 5:30:00 PM 8:05:00 AM

Run Finish Time 3:35:00 PM 11:20:00 PM 1:55:00 PM

Net Traversing Points 36 36 36

Net Run Time, minutes 365.9 366.6 358.8

Nozzle Diameter, inches 0.216 0.216 0.216 0.216

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.018 1.018 1.018 1.018

Barometric Pressure, inches of Mercury 29.74 29.74 29.85 29.777

Average Orifice Meter Differential, inches H2O 0.58 0.58 0.58 0.580

Dry Gas Meter Volume Sampled, cubic feet 125.925 127.315 126.363 126.534

Average Dry Gas Meter Temperature, °F 48.25 46.00 46.53 46.927

Dry Gas Meter Volume Sampled, dscf 132.562 134.621 133.967 133.717

Total Moisture Liquid collected, g 165.4 192.8 175.3 177.833

Volume of Water Vapor, standard cubic feet 7.79 9.08 8.25 8.373

Moisture Content of Stack Gas, % 5.55 6.32 5.80 5.890

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9445 0.9368 0.942 0.941

Carbon Dioxide, % 8.8 9 9.2 9.000

Oxygen, % 10.7 10.6 10.5 10.600

Carbon Monoxide & Nitrogen, % 80.5 80.4 80.3 80.400

Fuel Factor 1.16 1.14 1.13

Dry Molecular Weight, lb/lb-Mole 29.84 29.86 29.89 29.863

Wet Molecular weight, lb/lb-Mole 29.18 29.11 29.20 29.163

Flue Gas Static Pressure, inches of H2O -0.55 -0.55 -0.61 -0.570

Absolute Flue Gas Pressure, inches of Mercury 29.70 29.70 29.81 29.737

Average Stack Gas Temperature, °F 222.03 217.58 220.50 220.037

Average Velocity Head, inches of H2O 0.3306576644

08043

0.338006499

418845

0.331868891

496457

0.334

Average Stack Gas Velocity, feet/second 36.63 36.96 36.58 36.723

Stack Cross-Sectional Area, square feet 122.718 122.718 122.718 122.718

Dry Volumetric Flow Rate, dry scfm 195,759.9 197,199.8 196,137.3 196,365.667

Actual Wet Volumetric Flue Gas Flow Rate, acfm 269,709.6 272,139.4 269,341.5 270,396.833

Percent Isokinetic of Sampling Rate, % 89.2 89.8 91.8 90.267

Percent Excess Air, % 101.4 99.8 98.1 99.767

F-Factor, dscfm/MMBtu @ %O2 9459 9684 9629 9,590.667

Round Duct Diameter, inches 150 150 150

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw

Fc

Thursday, February 17, 2011 Page 29 of 29