### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, February 07, 2011 Page 1 of 7

### Facility Information:

Georgia Power-Plant Wansley 1371 Liberty Church Rd.

Carrollton Ga30116 Contact:Sarah Markham Phone: 205-257-6780 Fax: Email: sasander@southernco.com Testing Company: Weston Solutions 1625 Pumphrey Ave

Auburn Al36832 Contact:Jon Howard Phone:334-466-5600 Fax: 334-466-5660 Email: j.howard@westonsolutions.com

Air Permit Number: Permitted Source ID/Name: Plant Wansley Unit 2 2 Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rat

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: See Attached Report

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack 408.05 3600 5412 4 0 24 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Hydrogen Fluoride Method 26A 3 0 Stack Hydrogen Chloride Method 26A 3 0 Stack O2 Method 3A O2 3 0 Stack Co2 Method 3A CO2 3 0 Stack



### Monday, February 07, 2011 Page 2 of 7

### -Due to source being oversaturated, moisture was calculated using source temperature and pressure.

-Method 26A - Reference method requires a matrix spike, but this was not performed. -M26A/CTM-033 sample train was modified using 6N caustic in the caustic impinger, in order to keep final sample pH > 12, method requirement. The sample volumes are corrected for the CO2 concentration; due to the use of the strong caustic CO2 is removed from the gas stream. -Testing was conducted prior to the EPA FAQs page being updated, therefore, the reduced sample time and increased caustic strength and volume significantly raised the method detection limit for the CTM-033 component. - Please also note that the values presented in this database and the values in the hard copy report will vary slightly. We expect these differences are due to the fact that the ERT database recalculates all values.

Monday, February 07, 2011 Page 3 of 7

### Monday, February 07, 2011 Page 4 of 7

### Sampling / Stack Data Results Summary

Location Stack - Method 26A Average Run Number 1 2 3 Test Date 4/22/2010 4/22/2010 4/22/2010 Run Start Time 11:38:00 AM 12:58:00 PM 2:22:00 PM

Run Finish Time 12:48:00 PM2:09:00 PM 3:28:00 PM Net Run Time, minutes 60 60 60 Dry Gas Meter Volume Sampled, dscf 32.789 33.502 32.373 32.888 Moisture Content of Stack Gas, % 20.64 21.75 21.49 21.293 Moisture Saturation at Stack Gas Temperature, % 13.08 13.23 13.13 13.147 Carbon Dioxide, % 12.1 12.1 11.9 12.033 Oxygen, % 6.2 6.4 7.9 6.833 Average Stack Gas Temperature, °F 123.42 123.83 123.55 123.600 Dry Volumetric Flow Rate, dry scfm 1,938,251.71,947,595.1 1,958,638.01,948,161.60 0 Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,550,065.52,568,591.7 2,578,944.52,565,867.23 3 Percent Isokinetic of Sampling Rate, % 106.5 108.2 104.0 106.233 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Monday, February 07, 2011 Page 5 of 7

### Emissions Summary

Process Run Data Location: Stack - Method 26A Compound: Hydrogen Chloride Average RunNumber 1 2 3 Mass_mg 0.254 0.224 0.202 0.227 lb/mmBtuO2 2.37E-04 2.08E-04 2.16E-04 0.000 ppm 1.80E-01 1.56E-01 1.45E-01 0.160 

### Compound: Hydrogen Fluoride Average RunNumber 1 2 3 Mass_mg 0.0941 0.0645 0.049 0.069 lb/mmBtuO2 8.80E-05 5.98E-05 5.25E-05 0.000 ppm 1.22E-01 8.17E-02 6.43E-02 0.089



### Monday, February 07, 2011 Page 6 of 7

### Process Run Data

APCD Run Data

Process Lab Run Data

Monday, February 07, 2011 Page 7 of 7

### Sampling / Stack Data Results Detail

Location Stack - Method 26A Average Run Number 1 2 3 Test Date 4/22/2010 4/22/2010 4/22/2010 Run Start Time 11:38:00 AM12:58:00 PM 2:22:00 PM Run Finish Time 12:48:00 PM 2:09:00 PM 3:28:00 PM Net Traversing Points 13 13 12 Net Run Time, minutes 60 60 60 Nozzle Diameter, inches 0.21 0.21 0.21 0.210 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.988 0.988 0.988 0.988 Barometric Pressure, inches of Mercury 29 29 29 29.000 Average Orifice Meter Differential, inches H2O 1.03 1.07 1.07 1.057 Dry Gas Meter Volume Sampled, cubic feet 35.541 36.372 35.218 35.710 Average Dry Gas Meter Temperature, °F 89.50 90.42 91.55 90.490 Dry Gas Meter Volume Sampled, dscf 32.789 33.502 32.373 32.888 Total Moisture Liquid collected, g 181.3 197.8 188.2 189.100 Volume of Water Vapor, standard cubic feet 8.53 9.31 8.86 8.900 Moisture Content of Stack Gas, % 20.64 21.75 21.49 21.293 Moisture Saturation at Stack Gas Temperature, % 13.08 13.23 13.13 13.147 Dry Mole Fraction 0.8692 0.8677 0.8687 0.869 Carbon Dioxide, % 12.1 12.1 11.9 12.033 Oxygen, % 6.2 6.4 7.9 6.833 Carbon Monoxide & Nitrogen, % 81.7 81.5 80.2 81.133 Fuel Factor 1.21 1.20 1.09 Dry Molecular Weight, lb/lb-Mole 30.18 30.19 30.22 30.197 Wet Molecular weight, lb/lb-Mole 29.95 30.11 30.12 30.060 Flue Gas Static Pressure, inches of H2O -1.2 -1.2 -1.2 -1.200 Absolute Flue Gas Pressure, inches of Mercury 28.91 28.91 28.91 28.910 Average Stack Gas Temperature, °F 123.42 123.83 123.55 123.600 Average Velocity Head, inches of H2O 0.6303074239 121630.642526090

3965130.648330844

530336 0.640 Average Stack Gas Velocity, feet/second 46.80 47.14 47.33 47.090 Stack Cross-Sectional Area, square feet 908.143 908.143 908.143 908.143 Dry Volumetric Flow Rate, dry scfm 1,938,251.7 1,947,595.1 1,958,638.01,948,161.6 00 Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,550,065.5 2,568,591.7 2,578,944.52,565,867.2 33 Percent Isokinetic of Sampling Rate, % 106.5 108.2 104.0 106.233 Percent Excess Air, % 40.3 42.3 59.5 47.367 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Round Duct Diameter, inches 408.05 408.05 408.05 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10640 10640 1064010,640.000 Fc 1800 1800 1800 1,800.000



### Monday, February 07, 2011 Page 8 of 7