Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, February 09, 2011 Page 1 of 13
Facility Information:

Gulf Power Plant Crist

11999 Pate Street

Pensacola Fl 32514

Contact: Brandon Looney

Phone: 205-257-6162

Fax:

Email: mblooney@southernco.com

Testing Company:

Weston Solutions

1625 Pumphrey Ave

Auburn Al 36832

Contact:Jon Howard

Phone: 334-466-5600

Fax:

Email: j.howard@westonsolutions.com

Air Permit Number:

641

Permitted Source ID/Name:

4,5,6,7 Plant Crist Units 4,5,6,7

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

See attached report

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack 420 0 0 0 3800 3210 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Organic Condensible 

Particulate

Stack OTM - 28 3 0

Stack Total Particulate OTM - 28 3 0

Inorganic (Aqueous) 

Condensible Part.

Stack OTM - 28 3 0

Stack Lead Method 29 3 0

Stack Arsenic Method 29 3 0

Stack Beryllium Method 29 3 0

Wednesday, February 09, 2011 Page 2 of 13
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

See attached report

Stack Chromium Method 29 3 0

Stack Filterable Particulate Method 29 3 0

Stack Manganese Method 29 3 0

Stack Nickel Method 29 3 0

Stack Selenium Method 29 3 0

Stack Antimony Method 29 3 0

Stack Cobalt Method 29 3 0

Stack Phosphorus (yellow or white) Method 29 3 0

Stack Cadmium Method 29 3 0

Stack Filterable Particulate Method 5 3 0

Wednesday, February 09, 2011 Page 3 of 13
Sampling / Stack Data Results Summary

Location Stack - Method 29

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/28/2010

Run Start Time 12:40:00 PM 8:00:00 

AM

1:05:00 PM

Run Finish Time 5:28:00 PM 12:21:00 

PM

5:28:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 135.440 133.614 138.630 135.895

Moisture Content of Stack Gas, % 14.00 13.52 13.79 13.770

Moisture Saturation at Stack Gas Temperature, % 12.83 12.16 12.64 12.543

Carbon Dioxide, % 11.9 11 11.3 11.400

Oxygen, % 8.2 9.1 9 8.767

Average Stack Gas Temperature, °F 123.58 121.63 123.04 122.750

Dry Volumetric Flow Rate, dry scfm 2,717,323.5 2,681,812.8 2,734,352.9 2,711,163.06

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,482,656.6 3,399,530.1 3,493,624.7 3,458,603.80

0

Percent Isokinetic of Sampling Rate, % 99.4 99.3 101.1 99.933

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 09, 2011 Page 4 of 13
Location Stack - Method 5

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/28/2010

Run Start Time 12:40:00 PM 8:00:00 

AM

1:05:00 PM

Run Finish Time 5:28:00 PM 12:21:00 

PM

5:28:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 135.493 135.960 135.334 135.596

Moisture Content of Stack Gas, % 13.94 13.43 13.98 13.783

Moisture Saturation at Stack Gas Temperature, % 13.44 12.30 12.56 12.767

Carbon Dioxide, % 11.9 11 11.3 11.400

Oxygen, % 8.2 9.1 9 8.767

Average Stack Gas Temperature, °F 125.19 121.96 122.71 123.287

Dry Volumetric Flow Rate, dry scfm 2,608,423.6 2,713,223.8 2,681,377.9 2,667,675.10

0

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,382,789.3 3,453,793.2 3,427,816.2 3,421,466.23

3

Percent Isokinetic of Sampling Rate, % 103.6 99.9 100.6 101.367

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 09, 2011 Page 5 of 13
Location Stack - OTM - 28

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/28/2010

Run Start Time 12:40:00 PM 8:00:00 

AM

1:05:00 PM

Run Finish Time 5:21:00 PM 12:21:00 

PM

5:28:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 135.493 135.960 135.334 135.596

Moisture Content of Stack Gas, % 13.94 13.43 13.98 13.783

Moisture Saturation at Stack Gas Temperature, % 13.44 12.30 12.56 12.767

Carbon Dioxide, % 11.9 11 11.3 11.400

Oxygen, % 8.2 9.1 9 8.767

Average Stack Gas Temperature, °F 125.19 121.96 122.71 123.287

Dry Volumetric Flow Rate, dry scfm 2,608,423.6 2,713,223.8 2,681,377.9 2,667,675.10

0

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,382,789.3 3,453,793.2 3,427,816.2 3,421,466.23

3

Percent Isokinetic of Sampling Rate, % 103.6 99.9 100.6 101.367

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 09, 2011 Page 6 of 13
Emissions Summary

Location: Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0018 0.0018 0.0018 0.002

Elb/hr 4.78E-03 4.78E-03 4.70E-03 0.005

lb/mmBtuO2 4.72E-07 5.14E-07 4.92E-07 0.000

mg/dscm 4.69E-04 4.76E-04 4.59E-04 0.000

mg/dscm@7%O2 5.13E-04 5.61E-04 5.36E-04 0.001

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00202 0.00188 0.00263 0.002

Elb/hr 5.36E-03 4.99E-03 6.86E-03 0.006

lb/mmBtuO2 5.29E-07 5.37E-07 7.18E-07 0.000

mg/dscm 5.27E-04 4.97E-04 6.70E-04 0.001

mg/dscm@7%O2 5.77E-04 5.85E-04 7.83E-04 0.001

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00045 0.00045 0.00045 0.000

Elb/hr 1.19E-03 1.19E-03 1.17E-03 0.001

lb/mmBtuO2 1.18E-07 1.29E-07 1.23E-07 0.000

mg/dscm 1.17E-04 1.19E-04 1.15E-04 0.000

mg/dscm@7%O2 1.28E-04 1.40E-04 1.34E-04 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00045 0.00067 0.00045 0.001

Elb/hr 1.19E-03 1.78E-03 1.17E-03 0.001

lb/mmBtuO2 1.18E-07 1.91E-07 1.23E-07 0.000

mg/dscm 1.17E-04 1.77E-04 1.15E-04 0.000

mg/dscm@7%O2 1.28E-04 2.09E-04 1.34E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.00241 0.00173 0.00189 0.002

Elb/hr 6.40E-03 4.59E-03 4.93E-03 0.005

lb/mmBtuO2 6.31E-07 4.94E-07 5.16E-07 0.000

mg/dscm 6.28E-04 4.57E-04 4.82E-04 0.001

mg/dscm@7%O2 6.87E-04 5.38E-04 5.63E-04 0.001

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00118 0.00065 0.00094 0.001

Elb/hr 3.13E-03 1.73E-03 2.45E-03 0.002

Wednesday, February 09, 2011 Page 7 of 13
lb/mmBtuO2 3.09E-07 1.86E-07 2.57E-07 0.000

mg/dscm 3.08E-04 1.72E-04 2.39E-04 0.000

mg/dscm@7%O2 3.37E-04 2.03E-04 2.79E-04 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 7 7 6 6.667

Elb/hr 1.86E+01 1.86E+01 1.57E+01 17.633

lb/mmBtuO2 1.83E-03 2.00E-03 1.64E-03 0.002

mg/dscm 1.83E+00 1.85E+00 1.53E+00 1.737

mg/dscm@7%O2 2.00E+00 2.18E+00 1.79E+00 1.990

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.001 0.00093 0.00105 0.001

Elb/hr 2.65E-03 2.47E-03 2.74E-03 0.003

lb/mmBtuO2 2.62E-07 2.66E-07 2.87E-07 0.000

mg/dscm 2.61E-04 2.46E-04 2.68E-04 0.000

mg/dscm@7%O2 2.86E-04 2.90E-04 3.13E-04 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0035 0.0032 0.0033 0.003

Elb/hr 9.29E-03 8.50E-03 8.61E-03 0.009

lb/mmBtuO2 9.17E-07 9.15E-07 9.01E-07 0.000

mg/dscm 9.13E-04 8.46E-04 8.41E-04 0.001

mg/dscm@7%O2 9.99E-04 9.97E-04 9.82E-04 0.001

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.00331 0.00253 0.0023 0.003

Elb/hr 8.78E-03 6.72E-03 6.00E-03 0.007

lb/mmBtuO2 8.67E-07 7.23E-07 6.28E-07 0.000

mg/dscm 8.63E-04 6.69E-04 5.86E-04 0.001

mg/dscm@7%O2 9.45E-04 7.88E-04 6.84E-04 0.001

Compound: Phosphorus (yellow or white)

Average

RunNumber 1 2 3

Mass_mg 0.061805 0.048805 0.015155 0.042

Elb/hr 1.64E-01 1.30E-01 3.95E-02 0.111

lb/mmBtuO2 1.62E-05 1.39E-05 4.14E-06 0.000

mg/dscm 1.61E-02 1.29E-02 3.86E-03 0.011

mg/dscm@7%O2 1.76E-02 1.52E-02 4.51E-03 0.012

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0444 0.0499 0.0628 0.052

Elb/hr 1.18E-01 1.32E-01 1.64E-01 0.138

Wednesday, February 09, 2011 Page 8 of 13
Process Run Data

lb/mmBtuO2 1.16E-05 1.43E-05 1.72E-05 0.000

mg/dscm 1.16E-02 1.32E-02 1.60E-02 0.014

mg/dscm@7%O2 1.27E-02 1.55E-02 1.87E-02 0.016

Location: Stack - Method 5

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 14.1 18 18.4 16.833

Elb/hr 3.59E+01 4.75E+01 4.82E+01 43.867

lb/mmBtuO2 3.69E-03 5.06E-03 5.15E-03 0.005

Location: Stack - OTM - 28

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 15.9 6.8 7.2 9.967

Elb/hr 4.05E+01 1.80E+01 1.89E+01 25.800

lb/mmBtuO2 4.16E-03 1.91E-03 2.01E-03 0.003

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 5.1 4.9 4.1 4.700

Elb/hr 1.30E+01 1.29E+01 1.07E+01 12.200

lb/mmBtuO2 1.34E-03 1.38E-03 1.15E-03 0.001

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 20.9 11.8 11.2 14.633

Elb/hr 5.32E+01 3.11E+01 2.94E+01 37.900

lb/mmBtuO2 5.47E-03 3.31E-03 3.13E-03 0.004

Wednesday, February 09, 2011 Page 9 of 13
Process Run Data

APCD Run Data

Process Lab Run Data

Wednesday, February 09, 2011 Page 10 of 13
Sampling / Stack Data Results Detail

Location Stack - Method 29

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/28/2010

Run Start Time 12:40:00 PM 8:00:00 AM 1:05:00 PM

Run Finish Time 5:28:00 PM 12:21:00 PM 5:28:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.192 0.192 0.192 0.192

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.98 0.98 0.98 0.980

Barometric Pressure, inches of Mercury 29.6 29.6 29.6 29.600

Average Orifice Meter Differential, inches H2O 1.17 1.13 1.22 1.173

Dry Gas Meter Volume Sampled, cubic feet 145.158 142.786 149.109 145.684

Average Dry Gas Meter Temperature, °F 90.23 88.58 92.27 90.360

Dry Gas Meter Volume Sampled, dscf 135.440 133.614 138.630 135.895

Total Moisture Liquid collected, g 468.3 443.8 471.1 461.067

Volume of Water Vapor, standard cubic feet 22.04 20.89 22.17 21.700

Moisture Content of Stack Gas, % 14.00 13.52 13.79 13.770

Moisture Saturation at Stack Gas Temperature, % 12.83 12.16 12.64 12.543

Dry Mole Fraction 0.8717 0.8784 0.8736 0.875

Carbon Dioxide, % 11.9 11 11.3 11.400

Oxygen, % 8.2 9.1 9 8.767

Carbon Monoxide & Nitrogen, % 79.9 79.9 79.7 79.833

Fuel Factor 1.07 1.07 1.05

Dry Molecular Weight, lb/lb-Mole 30.23 30.12 30.17 30.173

Wet Molecular weight, lb/lb-Mole 28.87 28.89 28.84 28.867

Flue Gas Static Pressure, inches of H2O 0 0 0 0.000

Absolute Flue Gas Pressure, inches of Mercury 29.60 29.60 29.60 29.600

Average Stack Gas Temperature, °F 123.58 121.63 123.04 122.750

Average Velocity Head, inches of H2O 1.0334759575

3441

0.988660404

338011

1.039923687

53718

1.021

Average Stack Gas Velocity, feet/second 60.33 58.89 60.52 59.913

Stack Cross-Sectional Area, square feet 962.113 962.113 962.113 962.113

Dry Volumetric Flow Rate, dry scfm 2,717,323.5 2,681,812.8 2,734,352.9 2,711,163.0

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,482,656.6 3,399,530.1 3,493,624.7 3,458,603.8

00

Percent Isokinetic of Sampling Rate, % 99.4 99.3 101.1 99.933

Percent Excess Air, % 63.6 75.9 74.7 71.400

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 420 420 420

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 09, 2011 Page 11 of 13
Location Stack - Method 5

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/28/2010

Run Start Time 12:40:00 PM 8:00:00 AM 1:05:00 PM

Run Finish Time 5:28:00 PM 12:21:00 PM 5:28:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.192 0.192 0.192 0.192

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.972 0.996 0.996 0.988

Barometric Pressure, inches of Mercury 29.6 29.6 29.6 29.600

Average Orifice Meter Differential, inches H2O 1.07 1.21 1.19 1.157

Dry Gas Meter Volume Sampled, cubic feet 145.797 144.197 145.080 145.025

Average Dry Gas Meter Temperature, °F 87.79 93.44 99.38 93.537

Dry Gas Meter Volume Sampled, dscf 135.493 135.960 135.334 135.596

Total Moisture Liquid collected, g 466.2 448.1 467.2 460.500

Volume of Water Vapor, standard cubic feet 21.94 21.09 21.99 21.673

Moisture Content of Stack Gas, % 13.94 13.43 13.98 13.783

Moisture Saturation at Stack Gas Temperature, % 13.44 12.30 12.56 12.767

Dry Mole Fraction 0.8656 0.877 0.8744 0.872

Carbon Dioxide, % 11.9 11 11.3 11.400

Oxygen, % 8.2 9.1 9 8.767

Carbon Monoxide & Nitrogen, % 79.9 79.9 79.7 79.833

Fuel Factor 1.07 1.07 1.05

Dry Molecular Weight, lb/lb-Mole 30.23 30.12 30.17 30.173

Wet Molecular weight, lb/lb-Mole 28.68 28.83 28.90 28.803

Flue Gas Static Pressure, inches of H2O -0.75 -0.75 -0.75 -0.750

Absolute Flue Gas Pressure, inches of Mercury 29.54 29.54 29.54 29.540

Average Stack Gas Temperature, °F 125.19 121.96 122.71 123.287

Average Velocity Head, inches of H2O 0.9639211072

14192

1.015720155

03646

1.001601902

47406

0.994

Average Stack Gas Velocity, feet/second 58.60 59.83 59.38 59.270

Stack Cross-Sectional Area, square feet 962.113 962.113 962.113 962.113

Dry Volumetric Flow Rate, dry scfm 2,608,423.6 2,713,223.8 2,681,377.9 2,667,675.1

00

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,382,789.3 3,453,793.2 3,427,816.2 3,421,466.2

33

Percent Isokinetic of Sampling Rate, % 103.6 99.9 100.6 101.367

Percent Excess Air, % 63.6 75.9 74.7 71.400

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 420 420 420

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 09, 2011 Page 12 of 13
Location Stack - OTM - 28

Average

Run Number 1 2 3

Test Date 4/27/2010 4/28/2010 4/28/2010

Run Start Time 12:40:00 PM 8:00:00 AM 1:05:00 PM

Run Finish Time 5:21:00 PM 12:21:00 PM 5:28:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.192 0.192 0.192 0.192

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.972 0.996 0.996 0.988

Barometric Pressure, inches of Mercury 29.6 29.6 29.6 29.600

Average Orifice Meter Differential, inches H2O 1.07 1.21 1.19 1.157

Dry Gas Meter Volume Sampled, cubic feet 145.797 144.197 145.080 145.025

Average Dry Gas Meter Temperature, °F 87.79 93.44 99.38 93.537

Dry Gas Meter Volume Sampled, dscf 135.493 135.960 135.334 135.596

Total Moisture Liquid collected, g 466.2 448.1 467.2 460.500

Volume of Water Vapor, standard cubic feet 21.94 21.09 21.99 21.673

Moisture Content of Stack Gas, % 13.94 13.43 13.98 13.783

Moisture Saturation at Stack Gas Temperature, % 13.44 12.30 12.56 12.767

Dry Mole Fraction 0.8656 0.877 0.8744 0.872

Carbon Dioxide, % 11.9 11 11.3 11.400

Oxygen, % 8.2 9.1 9 8.767

Carbon Monoxide & Nitrogen, % 79.9 79.9 79.7 79.833

Fuel Factor 1.07 1.07 1.05

Dry Molecular Weight, lb/lb-Mole 30.23 30.12 30.17 30.173

Wet Molecular weight, lb/lb-Mole 28.68 28.83 28.90 28.803

Flue Gas Static Pressure, inches of H2O -0.75 -0.75 -0.75 -0.750

Absolute Flue Gas Pressure, inches of Mercury 29.54 29.54 29.54 29.540

Average Stack Gas Temperature, °F 125.19 121.96 122.71 123.287

Average Velocity Head, inches of H2O 0.9639211072

1419

1.015720155

03647

1.001601902

47406

0.994

Average Stack Gas Velocity, feet/second 58.60 59.83 59.38 59.270

Stack Cross-Sectional Area, square feet 962.113 962.113 962.113 962.113

Dry Volumetric Flow Rate, dry scfm 2,608,423.6 2,713,223.8 2,681,377.9 2,667,675.1

00

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,382,789.3 3,453,793.2 3,427,816.2 3,421,466.2

33

Percent Isokinetic of Sampling Rate, % 103.6 99.9 100.6 101.367

Percent Excess Air, % 63.6 75.9 74.7 71.400

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 420 420 420

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Wednesday, February 09, 2011 Page 13 of 13