Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 10143 9379 Inter-Power/AhlCon Partners, L.P. A/C Power-Colver Operations

legal owner2929 Allen Parkway, Suite 2200 Houston TX 77019

Page 1Facility _Information plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip Colver Power Project

141 Interpower Drive

Colver PA 15927 141 Interpower Drive Colver PA 15927

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas Don't Know FALSE FALSE FALSE FALSE TRUE FALSE FALSE FALSE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE TRUE None. No USEPA Region III This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 4Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 5Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SW test port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 6Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 7Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 8Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 9Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SW test port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 10Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 11Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 12Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 13Facility _Information This stack test was a paired train test. Run ID# 1, 2, 3 will represent the A train in the SSE test port.Run ID# 4,5,6 will represent the B train in the W SWtest port.Run ID#1 stack sample temp was 314 F on 10-7-08.Run ID#2 Stack sample temp was 314 F on 10-8-08.Run ID#3 stack sample temp was 315 F on 10-8-08.Run ID#4 stack sample temp was 311 F on 10-7-08.Run ID#5 stack sample temp was 315 F on 10-8-08.Run ID#6 stack sample temp was 318 F on 10-8-08.Run ID#1 stack sample temp was 311 F on 5-7-09.Run ID#2 stack sample temp was 311 F on 5-7-09.Run ID#3 stack sample temp was 311 F on 5-7-09.Run ID#1 stack sample temp was 308 F on 7-21-09.Run ID#2 stack sample temp was 303 F on 7-22-09.Run ID#3 stack sample temp was 306 F on 7-22-09.Run ID#4 stack sample temp was 308 F on 7-21-09.Run ID#5 stack sample temp was 303 F on 7-22-09.Run ID#6 stack sample temp was 306 F on 7-22-09.

Page 14facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 10143 1 Agent-for-IPAC, LP Dennis C. Simmers

814748796115 dsimmers@acpowercolver.com TRUE

Page 15facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note

Page 16facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type

Page 17facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain 10143 Wa ste Bituminous Coal

TRUE TRUE 700000 tons/year Yes The answer is yes pending a thorough due diligence investigation of 129's implications on every aspect of the business plan.

Page 18facility _other_materials rcra_explain The answer is yes pending a thorough due diligence investigation of 129's implications on every aspect of the business plan.

Page 19facility _other_materials The answer is yes pending a thorough due diligence investigation of 129's implications on every aspect of the business plan.

Page 20boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuel heat_input max_heat_input MW e_capacity 10143 AAB01 Fluidized bed firing Dry Bottom waste coal 8000 8000 131

Page 21boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 125 85.3 89 2525 2600 1005 1005 FALSE 1005

Page 22boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 1005 8112 96.05 Subpart Da(1) FALSE

Page 23boiler_information

NOx_control

SO2_control

combustion_additives Yes Yes No

Page 24boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 10143 AAB01 coal refuse 2007 100 100 10143 AAB01 coal refuse 2008 100 100 10143 AAB01 coal refuse 2009 100 100

Page 25boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 10143 AAB01 Fluidized Bed Com bustor 5/1/1995

Page 26boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 10143 AAB01 Lim estone injection to fluidized bed-fired furnace 5/1/1995

Page 27boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 28facility _units facility _id unit_id 10143 10143

Page 29unit_boilers

facility _id unit_id boiler_id 10143 10143 AAB01

Page 30facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 10143 AA01 NOx control Selective Noncataly

tic Reduction FALSE 5/1/1995 Am mo nia 10143 PM01 PM control Fabric Filter, pulse FALSE 5/1/1995

Page 31facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive 0

Page 32facility _sampling_ports facility _id sampling_port_id 10143 CEMW 01 10143 DPE01 10143 DPNW 01 10143 OPNW 01 10143 OPSE01 10143 SSE01 10143 WSW0 1

Page 33facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 10143 ST01 400 11.75 80

Page 34configurations

facility _id configuration_id 10143 AAB01

Page 35configuration_components

facility _id configuration_id

component_id

order component_type port_near 10143 AAB01 10143 1 Unit 10143 AAB01 AA01 2 NOx control 10143 AAB01 CEMW 01 11 Sam pling Port 10143 AAB01 DPE01 7 Sam pling Port 10143 AAB01 DPNW 01 8 Sam pling Port 10143 AAB01 OPNW 01 5 Sam pling Port 10143 AAB01 OPSE01 6 Sam pling Port 10143 AAB01 PM01 3 PM control 10143 AAB01 SSE01 9 Sam pling Port 10143 AAB01 ST01 4 Stack 10143 AAB01 WSW0 1 10 Sam pling Port

Page 36configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 10143 AAB01 Carbon Monoxide (CO) Federal - Title V Operating Permit

302 pound per hour (lb/hr)

1 hour 1258 tons per year (tons/yr) 10143 AAB01 PM (Filterable) Fderal - Title V Operating Permit

21.3 pound per hour (lb/hr)

1 hour 89 tons per year (tons/yr) 10143 AAB01 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

0.62 pound per million British Thermal Unit (lb/MMBtu)

24 hours 753 pound per hour (lb/hr) 10143 AAB01 VOCs Federal - Title V Operating Permit 11.2 pound per hour (lb/hr)

1 hour 47 tons per year (tons/yr) 10143 AAB01 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.2 pound per million British Thermal Unit (lb/MMBtu)

24 hours 243 pound per hour (lb/hr)

Page 37configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method 12 months 12 months No differentiation is made in the permit with regards to condensable or filterable PM. It simply states "particulate matter". 24 hours 0.94 pound per million British Thermal Unit (lb/MMBtu) 3 hours 1142 pound per hour (lb/hr) 3 hours Additional SO2 lim its: 2913 tons in any consecutive 12 month rolling average; SO2 reduction by at least 95% on a 30 day rolling average, with at least 92% removal in the boiler. 12 months 24 hours 932 tons per year (tons/yr)

Page 38configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting Continuous Emission Monitoring

5 years. Quarterly

and annual RATA. No differentiation is made in the permit with regards to condensable or filterable PM. It simply states "particulate matter". None. Additional SO2 lim its: 2913 tons in any consecutive 12 month rolling average; SO2 reduction by at least 95% on a 30 day rolling average, with at least 92% removal in the boiler. Continuous Emission Monitoring

5 years. Quarterly

and annual RATA.. None. Continuous Emission Monitoring

5 years. Quarterly

and annual RATA..

Page 39control_technologies

facility _id configuration_id

component_id

control_id project_title project_type vendor_name

vndor_contact

vendor_phone

Page 40control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 41control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 42control_technologies feed_rate_units

Page 43control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 44control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 45control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 46control_costs

CBI

Page 47mi sc_controls

facility _id mi sc_control_id

control_description

Page 48mi sc_control_configurations

facility _id mi sc_control_id

configuration_id

Page 49fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 10143 10-09 10/1/2009 58610 short tons (2000 lbs) coal PA PA - Cambria 10143 1-09 1/1/2009 66833 short tons (2000 lbs) coal PA PA - Cambria 10143 11-09 11/1/2009 56636 short tons (2000 lbs) coal PA PA - Cambria 10143 12-09 12/1/2009 62260 short tons (2000 lbs) coal PA PA - Cambria 10143 2-09 2/1/2009 58359 short tons (2000 lbs) coal PA PA - Cambria 10143 3-09 3/1/2009 51530 short tons (2000 lbs) coal PA PA - Cambria 10143 4-09 4/1/2009 46133 short tons (2000 lbs) coal PA PA - Cambria 10143 5-09 5/1/2009 60032 short tons (2000 lbs) coal PA PA - Cambria 10143 6-09 6/1/2009 60597 short tons (2000 lbs) coal PA PA - Cambria 10143 7-09 7/1/2009 62955 short tons (2000 lbs) coal PA PA - Cambria 10143 8-09 8/1/2009 60067 short tons (2000 lbs) coal PA PA - Cambria 10143 9-09 9/1/2009 58865 short tons (2000 lbs) coal PA PA - Cambria

Page 50fuel_shipments

coal_seam shipment_method Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks Kittananning and Freeport

Trucks

Page 51fuel_shipment_configurations

facility _id shipment_id

configuration_id 10143 10-09 AAB01 10143 1-09 AAB01 10143 11-09 AAB01 10143 12-09 AAB01 10143 2-09 AAB01 10143 3-09 AAB01 10143 4-09 AAB01 10143 5-09 AAB01 10143 6-09 AAB01 10143 7-09 AAB01 10143 8-09 AAB01 10143 9-09 AAB01

Page 52fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 10143 10-09 10-09 58610 tons 2.47 39.48 7291 Btu/lb 10143 1-09 1-09 66833 tons 2.44 45.1 6438 Btu/lb 10143 11-09 11-09 56636 tons 2.34 40.03 7267 Btu/lb 10143 12-09 12-09 62260 tons 2.41 44.31 6595 Btu/lb 10143 2-09 2-09 58359 tons 2.77 43.71 6688 Btu/lb 10143 3-09 3-09 51530 tons 2.81 44.81 6522 Btu/lb 10143 4-09 4-09 46133 tons 2.37 41.48 7085 Btu/lb 10143 5-09 5-09 60032 tons 2.26 40.42 7213 Btu/lb 10143 6-09 6-09 60597 tons 2.53 42.13 6912 Btu/lb 10143 7-09 7-09 62955 tons 2.52 41.93 6944 Btu/lb 10143 8-09 8-09 60067 tons 2.46 40.91 7164 Btu/lb 10143 9-09 9-09 58865 tons 2.4 40.71 7155 Btu/lb

Page 53fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive 520 parts per million (dry) (ppm) 175 parts per million (dry) (ppm)

permit requirements Other Colver Power Project 141 Interpower Drive

Page 54fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Nothern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No Colver PA 15927 Cardan Laboratories P.O. Box 541

Northern Cambria

PA 15714-0541No

Page 55fuel_shipment_samples analysis_copies

Page 56fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 57test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 10143 Mercury

Em issions 10-07 other Voluntary

Stack Testing for TRI Reporting Purposes Mercury stack emissions testing was conducted using ASTM D6784 (Ontario Hydro) test methods. ######## ######## Yes No 10143 Mercury

Em issions 10-2008 compliance Stack testing to comply with the Pennsylvania Mercury Reduction Rule. The test was performed using paired test trains. 10/7/2008 10/8/2008 Yes No 10143 Mercury

Em issions 8-2009 compliance Stack testing to comply with the Pennsylvania m ercury reduction rule.This test was performed with paired test trains. 7/21/2009 7/22/2009 Yes No 10143 PM Em issions 5-2009

compliance Three test runs were perfomed for the measurement of particulate emissions as the result of a PADEP request. 5/7/2009 5/7/2009 No No

Page 58test_reports

deviation_reports No No No No

Page 59test_report_configurations

facility _id report_id configuration_id 10143 Mercury

Em issions 10-07 AAB01 10143 Mercury

Em issions 10-2008 AAB01 10143 Mercury

Em issions 8-2009 AAB01 10143 PM Em issions 5-2009

AAB01

Page 60test_report_fuels

facility _id report_id fuel_id 10143 Mercury

Em issions 10-07 Wa ste bituminous coal 10143 Mercury

Em issions 10-2008 Wa ste bituminous coal 10143 Mercury

Em issions 8-2009 Wa ste bituminous coal 10143 PM Em issions 5-2009

Wa ste bituminous coal

Page 61test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 10143 Mercury

Em issions 10-07 Wa ste bituminous coal

coal refuse 100 100 10143 Mercury

Em issions 10-2008 Wa ste bituminous coal

coal refuse 100 100 10143 Mercury

Em issions 8-2009 Wa ste bituminous coal

coal refuse 100 100 10143 PM Em issions 5-2009

Wa ste bituminous coal

coal refuse 100 100

Page 62cem_data

facility _id tim e_period

cem_period_description 10143 2Q1995 through 4Q2009

Page 63cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 10143 2Q1995 through 4Q2009

Nitrogen Oxide (NOx) 10143 2Q1995 through 4Q2009

Sulfur Dioxide (SO2)

Page 64test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 10143 Mercury

Em issions 10-07 SSE01 No No 10143 Mercury

Em issions 10-2008 WSW0 1 No No 10143 Mercury

Em issions 8-2009 WSW0 1 No No 10143 PM Em issions 5-2009

SSE01 No No

Page 65test_report_sampling

fg_fraction

Page 66sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 10143 Mercury

Em issions 10-07 SSE01 1 ######## ######## 120.1 104 6.79 10143 Mercury

Em issions 10-2008 WSW0 1 1 10/7/2008 10/7/2008 124 108 6.8 10143 Mercury

Em issions 10-2008 WSW0 1 2 10/8/2008 10/8/2008 124 108 7.57 10143 Mercury

Em issions 10-2008 WSW0 1 3 10/8/2008 10/8/2008 124 108 7.07 10143 Mercury

Em issions 10-2008 WSW0 1 4 10/7/2008 10/7/2008 124 108 6.87 10143 Mercury

Em issions 10-2008 WSW0 1 5 10/8/2008 10/8/2008 124 108 7.57 10143 Mercury

Em issions 10-2008 WSW0 1 6 10/8/2008 10/8/2008 124 108 7.04 10143 Mercury

Em issions 8-2009 WSW0 1 1 7/21/2009 7/21/2009 124.6 108 7.55 10143 Mercury

Em issions 8-2009 WSW0 1 2 7/22/2009 7/22/2009 124.6 108 8.76 10143 Mercury

Em issions 8-2009 WSW0 1 3 7/22/2009 7/22/2009 124.6 108 8.34 10143 Mercury

Em issions 8-2009 WSW0 1 4 7/21/2009 7/21/2009 126.4 108 7.64 10143 Mercury

Em issions 8-2009 WSW0 1 5 7/22/2009 7/22/2009 124.6 108 8.71 10143 Mercury

Em issions 8-2009 WSW0 1 6 7/22/2009 7/22/2009 124.6 108 8.54 10143 PM Em issions 5-2009

SSE01 1 5/7/2009 5/7/2009 124.6 108 7.1 10143 PM Em issions 5-2009

SSE01 2 5/7/2009 5/7/2009 124.6 108 6.91 10143 PM Em issions 5-2009

SSE01 3 5/7/2009 5/7/2009 124.6 108 6.47

Page 67sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 302784 dscfm 28.14 6.5 13.5 1 283846 dscfm 28.17 5.7 14 1 283883 dscfm 27.76 5.3 13.4 1 290428 dscfm 27.76 5.3 13.2 1 288100 dscfm 28.17 5.7 14 1 283883 dscfm 27.76 5.3 13.4 1 288920 dscfm 27.76 5.3 13.2 1 3291526 dscfm 80 27.91 6.1 14.3 1 295643 dscfm 81 27.85 6.1 14.3 1 289637 dscfm 89 27.96 6.1 14.3 1 290744 dscfm 80 27.88 6.1 14.3 1 294772 dscfm 80 27.85 6.1 14.3 1 291087 dscfm 80 27.96 6.1 14.3 1 286275 dscfm 53 27.55 6 13.8 1 286883 dscfm 56 27.58 5.9 13.8 1 282658 dscfm 62 27.58 5.8 13.9 1

Page 68sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 28.08 ASTM D6784 (Ontario Hydro) None Wa ste bituminous coal 120.1 170000 41.72 7031 28.07 EPA Method 29 None. Wa ste bituminous coal 124 175000 43.67 6891 27.66 EPA Method 29 None. Wa ste bituminous coal 124 175000 45.03 6586 27.66 EPA Method 29 During run #3 a slight drop in sample train vacuum was briefly experienced. Sampling was stopped immediately and the integrtiy

of the sample train was checked through a leak check before resuming testing. No problems were found. Wa ste bituminous coal

124 175000 45.03 6586 28.07 EPA Method 29. Wa ste bituminous coal 124 175000 43.67 6891 27.66 EPA Method 29 Wa ste bituminous coal 124 175000 45.03 6586 27.66 EPA Method 29 During this run (third run) a slight drop in sample train vacuum was briefly experienced. Sampling was immediately stopped and the integrity of the sample train verified, and a leak check performed. No problems were noted. Sampling was resumed. Wa ste bituminous coal

124 175000 45.03 6586 27.82 EPA Method 29 Wa ste bituminous coal 124.6 180000 41.6 6972 27.75 EPA Method 29 Wa ste bituminous coal 124.6 180000 42.63 6928 27.86 Wa ste bituminous coal 124.6 180000 42.63 6928 27.79 EPA Method 29 Wa ste bituminous coal 124.6 180000 41.6 6972 27.76 EPA Method 29 Wa ste bituminous coal 124.6 180000 42.63 6928 27.87 Epa Method 29 Wa ste bituminous coal 124.6 180000 42.63 6928 27.45 USEPA Test Method 5 and USEPA OTM28. Wa ste bituminous coal

124.6 165000 39.5 7432 27.48 USEPA Method 5 and USEPA Methd OTM 28. None. Wa ste bituminous coal 124.6 165000 39.5 7432 27.49 USEPA Method 5 and USEPA Method OTM28 None. Wa ste bituminous coal 124.6 165000 39.5 7432

Page 69sampling_runs

fuel_sulfur 2.51 2.21 2.38 2.38 2.21 2.38 2.38 2.32 2.53 2.53 2.32 2.53 2.53 2.43 2.43 2.43

Page 70sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 10143 Mercury

Em issions 10-07 SSE01 1 Particulate-bound Mercury (Hgp) 1.09E-08 FALSE 10143 Mercury

Em issions 10-07 SSE01 1 Elem ental Mercury (Hg0) 9.97E-07 FALSE 10143 Mercury

Em issions 10-07 SSE01 1 Oxidized Mercury (Hg++) 7.24E-07 FALSE 10143 Mercury

Em issions 10-07 SSE01 1 Total Mercury (Hgt) 1.73E-06 FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 1 Total Mercury (Hgt) 0.09 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 2 Total Mercury (Hgt) 0.07 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 3 Total Mercury (Hgt) 0.12 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 4 Total Mercury (Hgt) 0.07 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 5 Total Mercury (Hgt) 0.06 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 6 Total Mercury (Hgt) 0.07 mi crogram per dry standard cubic meter ( FALSE 10143 PM Em issions 5-2009

SSE01 1 PM (Filterable) FALSE 10143 PM Em issions 5-2009

SSE01 1 PM (Condensable) FALSE 10143 PM Em issions 5-2009

SSE01 2 PM (Filterable) FALSE 10143 PM Em issions 5-2009

SSE01 2 PM (Condensable) FALSE 10143 PM Em issions 5-2009

SSE01 3 PM (Filterable) FALSE 10143 PM Em issions 5-2009

SSE01 3 PM (Condensable) FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 1 Total Mercury (Hgt) 0.014 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 2 Total Mercury (Hgt) 0.01 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 3 Total Mercury (Hgt) 0.015 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 4 Total Mercury (Hgt) 0.034 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 5 Total Mercury (Hgt) 0.01 mi crogram per dry standard cubic meter ( FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 6 Total Mercury (Hgt) 0.016 mi crogram per dry standard cubic meter ( FALSE

Page 71sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 0.000028 pound per hour (lb/hr) FALSE FALSE Concentration is gr./dscf 0.00259 pound per hour (lb/hr)

FALSE FALSE Concentration is gr./dscf 0.00188 pound per hour (lb/hr)

FALSE FALSE Concentration is gr./dscf 0.00449 pound per hour (lb/hr)

FALSE FALSE Concentration is gr./dscf 0.0001 pound per hour (lb/hr)

FALSE FALSE 0.00007 pound per hour (lb/hr)

FALSE FALSE 0.00013 pound per hour (lb/hr)

FALSE FALSE 0.0001 pound per hour (lb/hr)

FALSE FALSE 0.00007 pound per hour (lb/hr)

FALSE FALSE 0.00008 pound per hour (lb/hr)

FALSE FALSE 25.99 pound per hour (lb/hr)

FALSE 0.02 pound per million British Thermal Unit (lb/MMBtu) FALSE 60.71 pound per hour (lb/hr)

FALSE 0.047 pound per million British Thermal Unit (lb/MMBtu) FALSE 25.99 pound per hour (lb/hr)

FALSE 0.02 pound per million British Thermal Unit (lb/MMBtu) FALSE 3.08 pound per hour (lb/hr)

FALSE 0.001 pound per million British Thermal Unit (lb/MMBtu) FALSE 31.21 pound per hour (lb/hr)

FALSE 0.025 pound per million British Thermal Unit (lb/MMBtu) FALSE 60.21 pound per hour (lb/hr)

FALSE 0.0469 pound per million British Thermal Unit (lb/MMBtu) FALSE 0.00002 pound per hour (lb/hr)

FALSE FALSE 0.00001 pound per hour (lb/hr)

FALSE FALSE 0.00002 pound per hour (lb/hr)

FALSE FALSE 0.00004 pound per hour (lb/hr)

FALSE FALSE 0.00001 pound per hour (lb/hr)

FALSE FALSE 0.00002 pound per hour (lb/hr)

FALSE FALSE

Page 72sampling_run_pollutants1 run_pollutant_comment Concentration is gr./dscf Concentration is gr./dscf Concentration is gr./dscf Concentration is gr./dscf

Page 73sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL 10143 Mercury

Em issions 10-07 SSE01 1 Mercury (Hg) 0.92 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 1 Mercury (Hg) 0.8 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 2 Mercury (Hg) 0.84 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 3 Mercury (Hg) 0.84 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 4 Mercury (Hg) 0.8 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 5 Mercury (Hg) 0.84 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 10-2008 WSW0 1 6 Mercury (Hg) 0.84 mi crogram per gram (dry) (mg/g) FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 1 Mercury (Hg) 0.82 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 2 Mercury (Hg) 0.86 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 3 Mercury (Hg) 0.86 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 4 Mercury (Hg) 0.82 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 5 Mercury (Hg) 0.86 mi lligram per kilogram (dry) (mg/kg) FALSE 10143 Mercury

Em issions 8-2009 WSW0 1 6 Mercury (Hg) 0.86 mi lligram per kilogram (dry) (mg/kg) FALSE

Page 74sampling_run_fuel fuel_conc_MDL

Page 75