Instructions for Completing the Process Data Template

This template is to be used to record the 30 daily averages of specific process data required by the ICR. The ERT d

have the capability to store these daily averages. This spreadsheet included 4 separate surrogate worksheets, in 

boiler tested is tested for all surrogates at 4 different dates. This spreadsheet is intended to be used for one boi

facility. Data for multiple boilers should be handled by using separate copies of this spreadsheet.

yellow are required (if applicable to your boilers' operation). You do not need to populate cells shaded in gray, a

automatically populated from the Boiler Information worksheet. Please Do Not modify the structure of this spr

by adding or subtracting rows, columns, cells. Please name each resulting spreadsheet with the following nami

convention: [FacilityID]_Unit_[BoilerID]_Processdata.xls (example: 8100_Unit_2_Processdata.xls).

Please refer to the following steps when using these spreadsheets.

Boiler Information Worksheet

Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information workshee

Process Data Worksheets

Please use one process data worksheet for each HAP surrogate even is simultaneous testing of different HAP sur

was done. 
ta Template

s data required by the ICR. The ERT does not 

4 separate surrogate worksheets, in case the 

t is intended to be used for one boiler of one 

es of this spreadsheet. Fields shaded in 

d to populate cells shaded in gray, as they are 

Not modify the structure of this spreadsheet 

preadsheet with the following naming 

nit_2_Processdata.xls).

on the Boiler Information worksheet. 

taneous testing of different HAP surrogates 
EIA Facility Code Facility Name Boiler ID

963 Dallman 34
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date Coal Firing Rate Coal Firing Rate (units)

Day 1 6/9/2010 1506 Tons/day

Day 2 6/10/2010 1528.2 Tons/day

Day 3 6/11/2010 1534.2 Tons/day

Day 4 6/12/2010 1536.4 Tons/day

Day 5 6/13/2010 1370 Tons/day

Day 6 6/14/2010 1626.6 Tons/day

Day 7 6/15/2010 1592.5 Tons/day

Day 8 6/16/2010 1500 Tons/day

Day 9 6/17/2010 1451.5 Tons/day

Day 10 6/18/2010 1491.2 Tons/day

Day 11 6/19/2010 1491.7 Tons/day

Day 12 6/20/2010 1503.2 Tons/day

Day 13 6/21/2010 1559.2 Tons/day

Day 14 6/22/2010 1554.7 Tons/day

Day 15 6/23/2010 1621.6 Tons/day

Day 16 6/24/2010 1522.7 Tons/day

Day 17 6/25/2010 1217 Tons/day

Day 18 6/26/2010 1569 Tons/day

Day 19 6/27/2010 1516 Tons/day

Day 20 6/28/2010 1467 Tons/day

Day 21 6/29/2010 1477.8 Tons/day

Day 22 6/30/2010 1443.5 Tons/day

Day 23 7/1/2010 1465 Tons/day

Day 24 7/2/2010 1416.8 Tons/day

Day 25 7/3/2010 876.8 Tons/day

Day 26 7/4/2010 1476.9 Tons/day

Day 27 7/5/2010 1557.5 Tons/day

Day 28 7/6/2010 1551.9 Tons/day

Day 29 7/7/2010 1483 Tons/day

Day 30 7/8/2010 1152 Tons/day
ay Period Including the Testing Date

Average Heat Input (MMBtu/hr) Unit Net Electric Generation (MWh)

1582 150

1609 138

1611 137

1627 139

1432 117

1675 145

1645 142

1568 132

1529 127

1585 133

1587 134

1584 132

1634 138

1595 135

1658 141

1585 134

1375 107

1631 127

1546 129

1523 128

1538 129

1519 126

1544 129

1531 127

995 70

1547 129

1623 138

1630 139

1595 135

1322 104
Control Device Operating Parameters, As Appicable

Unit Gross Electric Generation (MWe) Flue Gas Flow Rate (dscfm) 

170 453,431

158 456,509

157 459,684

159 461,323

137 429,307

165 475,210

162 459,017

152 436,503

147 429,155

153 444,661

154 443,202

152 444,282

158 454,385

155 450,058

161 461,205

154 444,837

127 418,777

157 463,668

149 451,334

148 438,440

149 431,642

146 430,058

149 433,987

147 429,832

88 376,500

149 447,330

158 457,320

159 456,718

155 450,658

124 420,883
Pressure Drop across FGD (in H2O) FGD Scrubber Liquor Flow Rate (gals/min)

6.7 78.5

6.7 79.8

6.9 79.8

6.9 78.3

6.1 72

7.1 83.7

6.9 81.4

6.3 77.6

6.1 76.7

6.5 79

6.5 77.9

6.5 76.9

6.8 81.4

6.5 78.6

6.7 80.8

6.4 76

6 63.6

6.9 80.8

6.5 77.8

6.3 79.5

6.3 77.1

6.2 75.9

6.2 76

6.2 74.5

5.3 48.9

6.5 78.6

6.7 85.2

6.6 85.1

6.6 77.8

5.5 63.7
Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) 

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

29.8 137.1

29.8 137.5

29.8 138.8

29.9 138.8

29.9 137.8

29.8 138.9

29.8 138.7

29.9 138

29.9 137.8

29.9 138.8

29.9 138.1

30 138.9

30 139.4

29.9 139

29.9 140

30 138.2

29.9 136.7

29.8 138.2

29.6 137.8

29.7 137

30 137.1

30.1 136.1

30.1 136.3

30.1 136.9

29.9 132

29.9 137.5

29.8 138.1

29.9 138.1

30 139

29.9 136.6
Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

11

11.1

11.1

11.2

10.5

11.1

11.3

11.3

10.9

11.2

11.2

11.1

11.3

11.2

11.4

11

9.2

11.4

10.8

10.9

11.2

11

11.2

11

11.8

10.9

11.2

11.3

10.9

8.7
EIA Facility Code Facility Name Boiler ID

963 Dallman 34

Daily Average Process Data for a 30 Day Period Including the Testing Date

Date Coal Firing Rate Coal Firing Rate (units)

Day 1 6/9/2010 1506 Tons/day

Day 2 6/10/2010 1528.2 Tons/day

Day 3 6/11/2010 1534.2 Tons/day

Day 4 6/12/2010 1536.4 Tons/day

Day 5 6/13/2010 1370 Tons/day

Day 6 6/14/2010 1626.6 Tons/day

Day 7 6/15/2010 1592.5 Tons/day

Day 8 6/16/2010 1500 Tons/day

Day 9 6/17/2010 1451.5 Tons/day

Day 10 6/18/2010 1491.2 Tons/day

Day 11 6/19/2010 1491.7 Tons/day

Day 12 6/20/2010 1503.2 Tons/day

Day 13 6/21/2010 1559.2 Tons/day

Day 14 6/22/2010 1554.7 Tons/day

Day 15 6/23/2010 1621.6 Tons/day

Day 16 6/24/2010 1522.7 Tons/day

Day 17 6/25/2010 1217 Tons/day

Day 18 6/26/2010 1569 Tons/day

Day 19 6/27/2010 1516 Tons/day

Day 20 6/28/2010 1467 Tons/day

Day 21 6/29/2010 1477.8 Tons/day

Day 22 6/30/2010 1443.5 Tons/day

Day 23 7/1/2010 1465 Tons/day

Day 24 7/2/2010 1416.8 Tons/day

Day 25 7/3/2010 876.8 Tons/day

Day 26 7/4/2010 1476.9 Tons/day

Day 27 7/5/2010 1557.5 Tons/day

Day 28 7/6/2010 1551.9 Tons/day

Day 29 7/7/2010 1483 Tons/day

Day 30 7/8/2010 1152 Tons/day
ay Period Including the Testing Date

Average Heat Input (MMBtu/hr) Unit Net Electric Generation (MWh)

1582 150

1609 138

1611 137

1627 139

1432 117

1675 145

1645 142

1568 132

1529 127

1585 133

1587 134

1584 132

1634 138

1595 135

1658 141

1585 134

1375 107

1631 127

1546 129

1523 128

1538 129

1519 126

1544 129

1531 127

995 70

1547 129

1623 138

1630 139

1595 135

1322 104
Control Device Operating Parameters, As Appicable

Unit Gross Electric Generation (MWe) Flue Gas Flow Rate (dscfm) 

170 453,431

158 456,509

157 459,684

159 461,323

137 429,307

165 475,210

162 459,017

152 436,503

147 429,155

153 444,661

154 443,202

152 444,282

158 454,385

155 450,058

161 461,205

154 444,837

127 418,777

157 463,668

149 451,334

148 438,440

149 431,642

146 430,058

149 433,987

147 429,832

88 376,500

149 447,330

158 457,320

159 456,718

155 450,658

124 420,883
Pressure Drop across FGD (in H2O) FGD Scrubber Liquor Flow Rate (gals/min)

6.7 78.5

6.7 79.8

6.9 79.8

6.9 78.3

6.1 72

7.1 83.7

6.9 81.4

6.3 77.6

6.1 76.7

6.5 79

6.5 77.9

6.5 76.9

6.8 81.4

6.5 78.6

6.7 80.8

6.4 76

6 63.6

6.9 80.8

6.5 77.8

6.3 79.5

6.3 77.1

6.2 75.9

6.2 76

6.2 74.5

5.3 48.9

6.5 78.6

6.7 85.2

6.6 85.1

6.6 77.8

5.5 63.7
Other Boiler or Control Device Operating Parameters (e.g., Boiler O2) 

Flue Gas Pressure (atm) Flue Gas Sampling Point Temperature (Deg F)

29.8 137.1

29.8 137.5

29.8 138.8

29.9 138.8

29.9 137.8

29.8 138.9

29.8 138.7

29.9 138

29.9 137.8

29.9 138.8

29.9 138.1

30 138.9

30 139.4

29.9 139

29.9 140

30 138.2

29.9 136.7

29.8 138.2

29.6 137.8

29.7 137

30 137.1

30.1 136.1

30.1 136.3

30.1 136.9

29.9 132

29.9 137.5

29.8 138.1

29.9 138.1

30 139

29.9 136.6
Flue Gas Oxygen Content (%) Flue Gas Carbon Dioxide Content (%) Flue Gas Moisture Content (%)

11

11.1

11.1

11.2

10.5

11.1

11.3

11.3

10.9

11.2

11.2

11.1

11.3

11.2

11.4

11

9.2

11.4

10.8

10.9

11.2

11

11.2

11

11.8

10.9

11.2

11.3

10.9

8.7