Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

CPS Energy JT DEELY UNITS 1 AND 2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, January 28, 2011 Page 1 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Facility Information:

CPS Energy JT Deely Power Plant

9599 Gardner Rd.

San Antonio TX 78263

Contact: Mario Alvarez

Phone: 210-353-5818

Fax: 210-353-4883

Email: maalvarez@cpsenergy.com

Testing Company:

METCO Environmental

3226 Commander Dr.

Carrollton TX 75006

Contact: Ned Shappley

Phone: 972-931-7127

Fax: 972-931-8398

Email: nshappley@metcoenv.com

Air Permit Number:

90267

Permitted Source ID/Name:

E-3 JT Deely Units Number 1 and 2 Stack

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000464916 FRS #: 110000464916

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 312 0 0 312 4728 2832 4 16

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Filterable Particulate OTM - 27/28 3 400 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 400 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Friday, January 28, 2011 Page 2 of 15
CPS Energy JT DEELY UNITS 1 AND 2

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Total PM2.5 OTM - 27/28 3 400 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 400 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 400 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 400 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Mercury Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Cobalt Method 29 0

Stack Exit Phosphorus (yellow or white) Method 29 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Co2 Method 3A CO2 3 400 0

Stack Exit O2 Method 3A O2 3 400 0

Friday, January 28, 2011 Page 3 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Sampling / Stack Data Results Summary

Location Stack Exit - Method 29

Average

Run Number 1 2 3

Test Date 4/20/2010 4/21/2010 4/22/2010

Run Start Time 11:20:00 AM 8:00:00 

AM

7:40:00 AM

Run Finish Time 4:05:00 PM 12:40:00 

PM

12:10:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 169.022 168.113 168.836 168.657

Moisture Content of Stack Gas, % 12.31 12.70 12.87 12.627

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14.3 14.7 14.7 14.567

Oxygen, % 5.1 4.9 4.8 4.933

Average Stack Gas Temperature, °F 316.90 318.35 326.81 320.687

Dry Volumetric Flow Rate, dry scfm 2,046,191.0 2,004,642.5 1,967,244.1 2,006,025.86

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,535,031.5 3,505,724.2 3,499,034.5 3,513,263.40

0

Percent Isokinetic of Sampling Rate, % 92.8 94.2 96.4 94.467

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Exit - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, January 28, 2011 Page 4 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Friday, January 28, 2011 Page 5 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Emissions Summary

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0114 0.0036 0.0061 0.007

lb/mmBtuO2 1.92E-06 6.03E-07 1.01E-06 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00149 0.00098 0.00132 0.001

lb/mmBtuO2 2.51E-07 1.64E-07 2.19E-07 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.001 0.001 0.001 0.001

lb/mmBtuO2 1.69E-07 1.68E-07 1.66E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00116 0.00107 0.0015 0.001

lb/mmBtuO2 1.96E-07 1.79E-07 2.49E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.01616 0.00516 0.00306 0.008

lb/mmBtuO2 2.73E-06 8.64E-07 5.07E-07 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.01 0.01 0.01 0.010

lb/mmBtuO2 1.69E-06 1.68E-06 1.66E-06 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 17.3 9.3 7.7 11.433

lb/mmBtuO2 2.92E-03 1.56E-03 1.28E-03 0.002

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.003 0.00268 0.00259 0.003

lb/mmBtuO2 5.06E-07 4.49E-07 4.29E-07 0.000

Compound: Manganese

Average

Friday, January 28, 2011 Page 6 of 15
CPS Energy JT DEELY UNITS 1 AND 2

RunNumber 1 2 3

Mass_mg 0.00929 0.00492 0.0043 0.006

lb/mmBtuO2 1.57E-06 8.24E-07 7.13E-07 0.000

Compound: Mercury

Average

RunNumber 1 2 3

Mass_mg 0.03432 0.04605 0.03516 0.039

lb/mmBtuO2 5.79E-06 7.71E-06 5.83E-06 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.074 0.0348 0.0173 0.042

lb/mmBtuO2 1.25E-05 5.83E-06 2.87E-06 0.000

Compound: Phosphorus (yellow or white)

Average

RunNumber 1 2 3

Mass_mg 0.15045 0.12551 0.11774 0.131

lb/mmBtuO2 2.54E-05 2.10E-05 1.95E-05 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0381 0.017 0.0137 0.023

lb/mmBtuO2 6.43E-06 2.85E-06 2.27E-06 0.000

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 6.9 10.2 8.3 8.467

lb/mmBtuO2 1.62E-03 2.26E-03 1.87E-03 0.002

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 0.8 1.4 1.7 1.300

lb/mmBtuO2 1.88E-04 3.10E-04 3.82E-04 0.000

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 12.8 16.1 26.2 18.367

lb/mmBtuO2 3.01E-03 3.57E-03 5.89E-03 0.004

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 5 9.9 3.8 6.233

lb/mmBtuO2 1.18E-03 2.19E-03 8.55E-04 0.001

Friday, January 28, 2011 Page 7 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Process Run Data

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 23 34.2 36.3 31.167

lb/mmBtuO2 5.41E-03 7.58E-03 8.17E-03 0.007

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 16.6 25.4 29.7 23.900

lb/mmBtuO2 3.91E-03 5.63E-03 6.68E-03 0.005

Friday, January 28, 2011 Page 8 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Process Run Data

Run Name Value UOM Comments

Target

Value

4 Coal Burned 1018 1000 Tons/hr 0 Run 1

4 Average Heat Input 8380 MMBtu/hr 0 Run 1

4 Steam Output 5971 1000 lb steam/hr 0 Run 1

4 Flue Gas Oxygen Content 5.14 % Run 1 Collected 

by METCO 

Environmental

0

4 Flue Gas Carbon Dioxide Content 14.32 % Run 1 Collected 

by METCO 

Environmental

0

4 Flue Gas Moisture Content 12.18 % Run 1 Collected 

by METCO 

Environmental

0

4 Flue Gas Sampling Point Temperature 308 Deg F Run 1 Collected 

by METCO 

Environmental

0

4 Flue Gas Pressure 29.02 " Hg Run 1 Collected 

by METCO 

Environmental

0

4 Standard Pressure 29.92 "Hg 0 Run 1

4 Standard Temperature 68 Deg F 0 Run 1

4 Unit Gross Electrical Output 900 Mwe 0 Run 1

4 Unit Net Electric Generation 856 MWh 0 Run 1

5 Coal Burned 1013 1000 Tons/hr 0 Run 2

5 Average Heat Input 8380 MMBtu/hr 0 Run 2

5 Steam Output 5842 1000 lb steam/hr 0 Run 2

5 Flue Gas Oxygen Content 4.86 % Run 2, collected 

my METCo 

Environmental

0

5 Flue Gas Carbon Dioxide Content 14.68 % Run 2, collected 

my METCo 

Environmental

0

5 Flue Gas Moisture Content 12.65 % Run 2, collected 

my METCo 

Environmental

0

5 Flue Gas Sampling Point Temperature 315 Deg F Run 2, collected 

my METCo 

Environmental

0

5 Flue Gas Pressure 28.87 " Hg Run 2, collected 

my METCo 

Environmental

0

5 Standard Pressure 68 "Hg 0 Run 2

Friday, January 28, 2011 Page 9 of 15
CPS Energy JT DEELY UNITS 1 AND 2

APCD Run Data

Process Lab Run Data

5 Standard Temperature 29.92 Deg F 0 Run 2

5 Unit Gross Electrical Output 890 Mwe 0 Run 2

5 Unit Net Electric Generation 846 MWh 0 Run 2

6 Coal Burned 986 1000 Tons/hr 0 Run 3

6 Average Heat Input 8380 MMBtu/hr 0 Run 3

6 Steam Output 5747 1000 lb steam/hr 0 Run 3

6 Flue Gas Oxygen Content 4.82 % Run 3 collected by 

METCO 

Environmental

0

6 Flue Gas Carbon Dioxide Content 14.73 % Run 3 collected by 

METCO 

Environmental

0

6 Flue Gas Moisture Content 11.56 % Run 3 collected by 

METCO 

Environmental

0

6 Flue Gas Sampling Point Temperature 323 Deg F Run 3 collected by 

METCO 

Environmental

0

6 Flue Gas Pressure 28.74 " Hg Run 3 collected by 

METCO 

Environmental

0

6 Standard Pressure 29.92 "Hg 0 Run 3

6 Standard Temperature 68 Deg F 0 Run 3

6 Unit Gross Electrical Output 874 Mwe 0 Run 3

6 Unit Net Electric Generation 831 MWh 0 Run 3

Run Name Value UOM Comments

Target

Value

1 BAGHOUSE 0 0

1 OVERFIRE AIR 0 0

Run Name Value UOM Comments

3 Fuel Higher Heating Value 11972 Btu/lb

3 Fuel Moisture 30.53 %

3 Fuel Mercury Content 0.11 ppm

3 Fuel Cadmium Content 0.2 ppm

3 Ultimate/Proximate Analysis 0

3 Fuel Nickel Content 5 ppm

3 Fuel Arsenic Content 1 ppm

3 Fuel Chromium Content 6 ppm

Friday, January 28, 2011 Page 10 of 15
CPS Energy JT DEELY UNITS 1 AND 2

3 Fuel Beryllium Content 0.2 ppm

3 Fuel Lead Content 3 ppm

3 Fuel Manganese Content 17 ppm

3 Fuel Chlorine Content 14 ppm

3 Fuel Fluorine Content 58 ppm

3 Fuel Antimony Content 1 ppm

3 Fuel Selenium Content 1 ppm

4 Fuel Higher Heating Value 12705 Btu/lb

4 Fuel Moisture 30.06 %

4 Fuel Mercury Content 0.13 ppm

4 Fuel Cadmium Content 0.2 ppm

4 Ultimate/Proximate Analysis 0

4 Fuel Nickel Content 5 ppm

4 Fuel Arsenic Content 1 ppm

4 Fuel Chromium Content 6 ppm

4 Fuel Beryllium Content 0.2 ppm

4 Fuel Lead Content 3 ppm

4 Fuel Manganese Content 14 ppm

4 Fuel Chlorine Content 12 ppm

4 Fuel Fluorine Content 61 ppm

4 Fuel Antimony Content 1 ppm

4 Fuel Selenium Content 1 ppm

5 Fuel Higher Heating Value 12021 Btu/lb

5 Fuel Moisture 29.86 %

5 Fuel Mercury Content 0.08 ppm

5 Fuel Cadmium Content 0.2 ppm

5 Ultimate/Proximate Analysis 0

5 Fuel Nickel Content 4 ppm

5 Fuel Arsenic Content 1 ppm

5 Fuel Chromium Content 5 ppm

5 Fuel Beryllium Content 0.2 ppm

5 Fuel Lead Content 2 ppm

5 Fuel Manganese Content 12 ppm

5 Fuel Chlorine Content 11 ppm

5 Fuel Fluorine Content 61 ppm

5 Fuel Antimony Content 1 ppm

5 Fuel Selenium Content 1 ppm

Friday, January 28, 2011 Page 11 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Sampling / Stack Data Results Detail

Location Stack Exit - Method 29

Average

Run Number 1 2 3

Test Date 4/20/2010 4/21/2010 4/22/2010

Run Start Time 11:20:00 AM 8:00:00 AM 7:40:00 AM

Run Finish Time 4:05:00 PM 12:40:00 PM 12:10:00 PM

Net Traversing Points 49 49 49

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.19 0.19 0.19 0.190

Pitot Tube Coefficient 0.82 0.82 0.82 0.820

Dry Gas Meter Calibration Factor 0.989 0.989 0.989 0.989

Barometric Pressure, inches of Mercury 29.22 29.11 28.97 29.100

Average Orifice Meter Differential, inches H2O 1.77 1.82 1.78 1.790

Dry Gas Meter Volume Sampled, cubic feet 178.223 178.037 180.259 178.840

Average Dry Gas Meter Temperature, °F 80.13 80.52 82.26 80.970

Dry Gas Meter Volume Sampled, dscf 169.022 168.113 168.836 168.657

Total Moisture Liquid collected, g 503.9 519.4 529.8 517.700

Volume of Water Vapor, standard cubic feet 23.72 24.45 24.94 24.370

Moisture Content of Stack Gas, % 12.31 12.70 12.87 12.627

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8769 0.873 0.8713 0.874

Carbon Dioxide, % 14.3 14.7 14.7 14.567

Oxygen, % 5.1 4.9 4.8 4.933

Carbon Monoxide & Nitrogen, % 80.6 80.4 80.5 80.500

Fuel Factor 1.10 1.09 1.10

Dry Molecular Weight, lb/lb-Mole 30.49 30.55 30.54 30.527

Wet Molecular weight, lb/lb-Mole 28.95 28.96 28.93 28.947

Flue Gas Static Pressure, inches of H2O -2.23 -2.95 -2.78 -2.653

Absolute Flue Gas Pressure, inches of Mercury 29.06 28.89 28.77 28.907

Average Stack Gas Temperature, °F 316.90 318.35 326.81 320.687

Average Velocity Head, inches of H2O 2.7134179382

2224

2.648928281

60154

2.597237226

31198

2.653

Average Stack Gas Velocity, feet/second 110.97 110.05 109.84 110.287

Stack Cross-Sectional Area, square feet 530.929 530.929 530.929 530.929

Dry Volumetric Flow Rate, dry scfm 2,046,191.0 2,004,642.5 1,967,244.1 2,006,025.8

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,535,031.5 3,505,724.2 3,499,034.5 3,513,263.4

00

Percent Isokinetic of Sampling Rate, % 92.8 94.2 96.4 94.467

Percent Excess Air, % 31.5 30.0 29.2 30.233

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 312 312 312

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 28, 2011 Page 12 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, January 28, 2011 Page 13 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, January 28, 2011 Page 14 of 15
CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, January 28, 2011 Page 15 of 15