Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_ty pe

legal_address

legal_city legal_state legal_zip 2917 2917 City

of Hamilton City of Hamilton operator 960 N. Third Street Hamilton OH 45011

Page 1Facility _Information plant_nam e

physical_address

phyical_city

physical_state

physical_zip

ma iling_address

ma iling_city

ma iling_state

ma iling_zip Hamilton 960 N. Third Street Hamilton OH 45011 960 N. Third Street Hamilton OH 45011

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE FALSE TRUE FALSE FALSE TRUE FALSE TRUE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE Sum ma ry of Deviation Reporting Required for Violations of Permit Requirements (also refer to the attached Title V Operating Permit for additional details):[1] Quarterly Deviation Reports documenting all instances of opacity excursions detailing the date, commencement and completion times, duration, magnitude (percent opacity ), reason (if known), and corrective action(s) taken (if any) of each 6-minute block average above the applicable opacity lim itation. These reports also identify any excursions of the start-up and shutdown provisions specified in 3745-17-07(A)(3) and document any continuous opacity

monitoring system downtime while the emissions unit was on line (date, time, duration and reason), along with any corrective action(s) taken.[2] Quarterly Deviation Reports documenting and detailing the date, commencement and completion times, duration, magnitude, reason (if known), and corrective action(s) taken (if any ) of all 3-hour average sulfur dioxide values in excess of the applicable sulfur dio No Subm itted Electronically via the U.S. EPA Em issions Collection and Monitoring Plan System (ECMPS)ECMPS Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 4Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 5Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 6Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 7Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 8Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 9Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 10Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 11Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 12Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 13Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 14Facility _Information Part I - Boiler Information:No "Design" or "Operating" steam reheat cycles are utilized in conjunction with Unit 9. Therefore, these fields were left blank.________________________________________________________________________________________Part I - Boiler Information: Boiler Fuels TabUnit 9 burns both coal and natural gas. Per ICR FAQ EICR-027 guidance, a value of "0" was placed in the fields for "percentage on a mass or volume basis" and the correct percentage splits were entered in the "Percentage on Btu basis" fields.________________________________________________________________________________________Part I - FacilityUnits Configuration: Sampling PortsThe Unit 9 Stack (S9) has one (1) test platform with a height of 136 feet above ground level. At this test platform location, there are a total of four (4) sampling ports around the stack (SP1, SP2, SP3, SP4). ________________________________________________________________________________________Part I - Unit Informa

Page 15facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 2917 1 Manager of Power Plant Operations Daniel F. Moats

5137857456

5137857450

mo atsd@ci.hamilton.oh.us

TRUE

Page 16facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 2917 bitum inous 100 100

Page 17facility _oil_utilized facility _id oil_ty pe percentage_volume percentage_btu

other_type

Page 18facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 19facility _other_materials rcra_explain

Page 20boiler_information

facility _id boiler_id boiler_ty pe boiler_other bottom_design

design_fuel heat_input ma x_heat_input MW e_capacity 2917 9 Tangential firing Dry Bottom coal 729 729 50.6

Page 21boiler_information

MW e_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 48 87 83 1250 1250 960 960 FALSE

Page 22boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 6065 52.9 Subpart D 2025 FALSE

Page 23boiler_information

NOx_control

SO2_control

combustion_additives Yes Yes No

Page 24boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 2917 9 coal - bituminous 2007 0 98.4 2917 9 coal - bituminous 2008 0 98.6 2917 9 coal - bituminous 2009 0 96.8 2917 9 natural gas 2007 0 1.6 2917 9 natural gas 2008 0 1.4 2917 9 natural gas 2009 0 3.2

Page 25boiler_control_NOx

facility _id boiler_id NOx_ty pe NOx_other NOx_online 2917 9 Advanced Overfire Air 4/1/2001 2917 9 Low NOx Burner 6/1/2000

Page 26boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 2917 9 Other (specify) Coal Blending (W ashed High Sulfur and W ashed Compliance Coal)

12/1/2004

Page 27boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 28facility _units facility _id unit_id 2917 9

Page 29unit_boilers

facility _id unit_id boiler_id 2917 9 9

Page 30facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 2917 9_BH PM control Fabric Filter, pulse FALSE 1/1/1997 2917 9_Cyclone PM control Single cyclone FALSE 1/1/1997 2917 9_ESP PM control Electrostatic precipitator, hot side, w/o flue gas conditioning FALSE 6/1/1974 2917 9_FGD SO2 control Spray dryer type FALSE 6/1/2001

Page 31facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive Lim e No

Page 32facility _sampling_ports facility _id sampling_port_id 2917 SP1 2917 SP2 2917 SP3 2917 SP4

Page 33facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 2917 S9 166 10.41 43.6

Page 34configurations

facility _id configuration_id 2917 Unit 9

Page 35configuration_components

facility _id configuration_id

component_id

order component_ty pe port_near 2917 Unit 9 9 1 Unit 2917 Unit 9 9_BH 5 PM control 2917 Unit 9 9_Cyclone 4 PM control 2917 Unit 9 9_ESP 2 PM control 2917 Unit 9 9_FGD 3 SO2 control 2917 Unit 9 S9 6 Stack

Page 36configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_ty pe_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 2917 Unit 9 PM (Filterable) Fderal - Title V Operating Permit

0.1 pound per million British Thermal Unit (lb/MMBtu)

NA 319 tons per year (tons/yr) 2917 Unit 9 Sulfur Dioxide (SO2) Federal - Title V Operating Permit

1.2 pound per million British Thermal Unit (lb/MMBtu)

3 hours 3832 tons per year (tons/yr) 2917 Unit 9 Nitrogen Oxide (NOx) Federal - Title V Operating Permit

0.7 pound per million British Thermal Unit (lb/MMBtu)

3 hours 2235 tons per year (tons/yr) 2917 Unit 9 Carbon Monoxide (CO) Federal - Title V Operating Permit

16.2 pound per hour (lb/hr)

1 hour 71 tons per year (tons/yr) 2917 Unit 9 Total Hydrocarbons (THC) (as Methane) Federal - Title V Operating Permit

1.94 pound per hour (lb/hr)

1 hour 8.5 tons per year (tons/yr)

Page 37configuration_pollutants1

avg_period_2

em lim it_3 em lim it_units_3 avg_period_3

em lim it_4 em lim it_units_4 avg_period_4

em lim it_details

test_method Annual Lim it 2: Lim it per Ohio EPA (PTI 14-4614) Method 5 Annual Lim it 2: Lim it per Ohio EPA (PTI 14-4614) Annual 0.4 pound per million British Thermal Unit (lb/MMBtu) 3 hours Lim it 2 per Ohio EPA (PTI 14-4614); Limit 3 per Title IV Acid Rain Permit (OAC Chapter 3745-103) Annual Lim its 1 & 2: Limits per Ohio EPA (PTI 14-4614) Annual Lim its 1 & 2 (specified for organic compound emissions): Limits per Ohio EPA (PTI 14-4614)

Page 38configuration_pollutants1

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping

req_reporting No No guaranteed emission rate was sought or is available Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Lim it 2: Lim it per Ohio EPA (PTI 14-4614) No No guaranteed emission rate was sought or is available Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Lim it 2 per Ohio EPA (PTI 14-4614); Limit 3 per Title IV Acid Rain Permit (OAC Chapter 3745-103) No No guaranteed emission rate was sought or is available Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Lim its 1 & 2: Limits per Ohio EPA (PTI 14-4614) No No guaranteed emission rate was sought or is available Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Lim its 1 & 2 (specified for organic compound emissions): Limits per Ohio EPA (PTI 14-4614) No No guaranteed emission rate was sought or is available Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Page 39configuration_pollutants1 Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009 Reference Attached Federal Title V Operating Permit for Emissions Unit ID B009

Page 40control_technologies

facility _id configuration_id

component_id

control_id project_title project_ty pe vendor_name

vndor_contact

vendor_phone

Page 41control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 42control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 43control_technologies feed_rate_units

Page 44control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 45control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 46control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 47control_costs

CBI

Page 48mi sc_controls

facility _id mi sc_control_id

control_description

Page 49mi sc_control_configurations

facility _id mi sc_control_id

configuration_id

Page 50fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 2917 Aug2009-Comp

8/1/2009 8764 short tons (2000 lbs) coal WV WV- Kanawha 2917 Aug2009-HS 8/1/2009 7597 short tons (2000 lbs) coal OH OH - Belmont 2917 Dec2009-Comp

12/1/2009 4822 short tons (2000 lbs) coal WV WV- Kanawha 2917 Dec2009-HS

12/1/2009 4052 short tons (2000 lbs) coal OH OH - Belmont 2917 Feb2009-Comp

2/1/2009 9758 short tons (2000 lbs) coal WV WV- Kanawha 2917 Feb2009-HS 2/1/2009 2160 short tons (2000 lbs) coal OH OH - Belmont 2917 Jan2009-Comp

1/1/2009 10770 short tons (2000 lbs) coal WV WV- Kanawha 2917 Jul2009-Comp

7/1/2009 8046 short tons (2000 lbs) coal WV WV- Kanawha 2917 Jul2009-HS 7/1/2009 8345 short tons (2000 lbs) coal OH OH - Belmont 2917 Jun2009-Comp

6/1/2009 9992 short tons (2000 lbs) coal WV WV- Kanawha 2917 Jun2009-HS 6/1/2009 4376 short tons (2000 lbs) coal OH OH - Belmont 2917 Mar2009-Comp

3/1/2009 4942 short tons (2000 lbs) coal WV WV- Kanawha 2917 Mar2009-HS 3/1/2009 2689 short tons (2000 lbs) coal OH OH - Belmont 2917 May2009-Comp

5/1/2009 8122 short tons (2000 lbs) coal WV WV- Kanawha 2917 Sep2009-Comp

9/1/2009 8466 short tons (2000 lbs) coal WV WV- Kanawha 2917 Sep2009-HS 9/1/2009 5222 short tons (2000 lbs) coal OH OH - Belmont

Page 51fuel_shipments

coal_seam shipment_method Campbells Creek #7 Mine

Trucks Powhatten #6 Mine

Trucks Campbells Creek #7 Mine

Trucks Powhatten #6 Mine

Trucks Campbells Creek #7 Mine

Trucks Powhatten #6 Mine

Trucks Campbells Creek #7 Mine

Trucks Campbells Creek #7 Mine

Trucks Powhatten #6 Mine

Trucks Campbells Creek #7 Mine

Trucks Powhatten #6 Mine

Trucks Campbells Creek #7 Mine

Trucks Powhatten #6 Mine

Trucks Campbells Creek #7 Mine

Trucks Campbells Creek #7 Mine

Trucks Powhatten #6 Mine

Trucks

Page 52fuel_shipment_configurations

facility _id shipment_id

configuration_id 2917 Aug2009-Comp

Unit 9 2917 Aug2009-HS

Unit 9 2917 Dec2009-Comp

Unit 9 2917 Dec2009-HS

Unit 9 2917 Feb2009-Comp

Unit 9 2917 Feb2009-HS

Unit 9 2917 Jan2009-Comp

Unit 9 2917 Jul2009-Comp

Unit 9 2917 Jul2009-HS

Unit 9 2917 Jun2009-Comp

Unit 9 2917 Jun2009-HS

Unit 9 2917 Mar2009-Comp

Unit 9 2917 Mar2009-HS

Unit 9 2917 May2009-Comp

Unit 9 2917 Sep2009-Comp

Unit 9 2917 Sep2009-HS

Unit 9

Page 53fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units 2917 Aug2009-Comp

8-1CB 442 tons 0.88 11.88 12980 Btu/lb 2917 Aug2009-HS

8-1CBHS 445 tons 3.51 10.78 13021 Btu/lb 2917 Dec2009-Comp

12-1CB 440 tons 0.83 13.63 12977 Btu/lb 2917 Dec2009-Comp

12-2CB 420 tons 0.82 13.83 12827 Btu/lb 2917 Dec2009-HS

12-1CBHS 441 tons 3.37 10.67 13261 Btu/lb 2917 Feb2009-Comp

2-1CB 436 tons 0.7 12.65 13019 Btu/lb 2917 Feb2009-Comp

2-1CNet 450 tons 0.66 10.62 13432 Btu/lb 2917 Feb2009-HS

2-1CBHS 434 tons 4.07 10.01 13168 Btu/lb 2917 Jan2009-Comp

1-1CB 476 tons 0.72 10.18 13538 Btu/lb 2917 Jul2009-Comp

7-1CB 440 tons 0.91 10.98 13372 Btu/lb 2917 Jul2009-HS

7-16CBHS 451 tons 3.77 10.45 13223 Btu/lb 2917 Jun2009-Comp

6-1CB 445 tons 0.75 9.08 13609 Btu/lb 2917 Mar2009-Comp

3-1CB 455 tons 0.72 12.23 12989 Btu/lb 2917 May2009-Comp

5-1CB 454 tons 0.76 12.89 13012 Btu/lb 2917 Sep2009-Comp

9-1CB 449 tons 0.95 8.92 12972 Btu/lb 2917 Sep2009-HS

9-1CBHS 456 tons 2.18 11.2 12961 Btu/lb

Page 54fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_ty pe

supplier_name

supplier_address contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street contractual obligations Other City of Hamilton Municipal Power Plant 960 N. Third Street

Page 55fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 2979 East Center Street

Conneaut OH 44030 Yes Hamilton OH 45011 SGS North America Inc. 2979 East Center Street

Conneaut OH 44030 Yes Hamilton OH 45011 SGS North America Inc. 2979 East Center Street

Conneaut OH 44030 Yes Hamilton OH 45011 SGS North America Inc. 2979 East Center Street

Conneaut OH 44030 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 2979 East Center Street

Conneaut OH 44030 Yes Hamilton OH 45011 SGS North America Inc. 2979 East Center Street

Conneaut OH 44030 Yes Hamilton OH 45011 SGS North America Inc. 2979 East Center Street

Conneaut OH 44030 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes Hamilton OH 45011 SGS North America Inc. 16130 Van Drunen Road

South Holland

IL 60473 Yes

Page 56fuel_shipment_samples analysis_copies

Page 57fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL 2917 Aug2009-Comp

8-1CB Mercury

(Hg) 0.05 mi crogram per gram (dry) (mg/g) FALSE 2917 Aug2009-HS

8-1CBHS Mercury

(Hg) 0.06 mi crogram per gram (dry) (mg/g) FALSE 2917 Dec2009-Comp

12-1CB Mercury

(Hg) 0.08 mi crogram per gram (dry) (mg/g) FALSE 2917 Dec2009-Comp

12-2CB Mercury

(Hg) 0.06 mi crogram per gram (dry) (mg/g) FALSE 2917 Dec2009-HS

12-1CBHS Mercury

(Hg) 0.09 mi crogram per gram (dry) (mg/g) FALSE 2917 Feb2009-Comp

2-1CB Mercury

(Hg) 0.04 mi crogram per gram (dry) (mg/g) FALSE 2917 Feb2009-Comp

2-1CNet Mercury

(Hg) 0.06 mi crogram per gram (dry) (mg/g) FALSE 2917 Feb2009-HS

2-1CBHS Mercury

(Hg) 0.11 mi crogram per gram (dry) (mg/g) FALSE 2917 Jan2009-Comp

1-1CB Mercury

(Hg) 0.04 mi crogram per gram (dry) (mg/g) FALSE 2917 Jul2009-Comp

7-1CB Mercury

(Hg) 0.08 mi crogram per gram (dry) (mg/g) FALSE 2917 Jul2009-HS

7-16CBHS Mercury

(Hg) 0.09 mi crogram per gram (dry) (mg/g) FALSE 2917 Jun2009-Comp

6-1CB Mercury

(Hg) 0.05 mi crogram per gram (dry) (mg/g) FALSE 2917 Mar2009-Comp

3-1CB Mercury

(Hg) 0.04 mi crogram per gram (dry) (mg/g) FALSE 2917 May2009-Comp

5-1CB Mercury

(Hg) 0.05 mi crogram per gram (dry) (mg/g) FALSE 2917 Sep2009-Comp

9-1CB Mercury

(Hg) 0.05 mi crogram per gram (dry) (mg/g) FALSE 2917 Sep2009-HS

9-1CBHS Mercury

(Hg) 0.07 mi crogram per gram (dry) (mg/g) FALSE

Page 58test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 2917 U9-Particulate

compliance Title V Operating Permit - Compliance Particulate Test Report for City of Hamilton Unit 9 5/28/2008 5/30/2008 No No

Page 59test_reports

deviation_reports No

Page 60test_report_configurations

facility _id report_id configuration_id 2917 U9-Particulate

Unit 9

Page 61test_report_fuels

facility _id report_id fuel_id 2917 U9-Particulate

Coal

Page 62test_report_fuel_ty pes

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type 2917 U9-Particulate

Coal coal - bituminous 100 100

Page 63cem_data

facility _id tim e_period

cem_period_description 2917 2000- present

Continuous Emissions Monitoring (CEMs) Data for sulfur dioxide emissions, nitrogen dioxide emissions and carbon dioxide emissions. There is also a Continuous Opacity Monitor associated with Unit 9.

Page 64cem_data Continuous Emissions Monitoring (CEMs) Data for sulfur dioxide emissions, nitrogen dioxide emissions and carbon dioxide emissions. There is also a Continuous Opacity Monitor associated with Unit 9.

Page 65cem_data Continuous Emissions Monitoring (CEMs) Data for sulfur dioxide emissions, nitrogen dioxide emissions and carbon dioxide emissions. There is also a Continuous Opacity Monitor associated with Unit 9.

Page 66cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 2917 2000- present

Nitrogen Oxide (NOx) 2917 2000- present

Sulfur Dioxide (SO2)

Page 67test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_by pass_percent

testing_by pass_percent 2917 U9-Particulate

S9 No There was no special placement of the sampling port in reference to the unit configuration in Part I. However:Runs 1-3 were conducted with the scrubber operating (Scrubber On).Runs 4-6 were conducted with the scrubber NOT operating (Scrubber OFF) No

Page 68test_report_sampling

fg_fraction All of the flue gas (100%) exits through this stack.

Page 69sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 2917 U9-Particulate

S9 1 5/28/2008 5/28/2008 50.8 57.9 12.4 2917 U9-Particulate

S9 2 5/28/2008 5/28/2008 51 56.5 12.28 2917 U9-Particulate

S9 3 5/28/2008 5/28/2008 50.9 56.5 12.58 2917 U9-Particulate

S9 4 5/30/2008 5/30/2008 50.3 58.9 7.11 2917 U9-Particulate

S9 5 5/30/2008 5/30/2008 50.2 54 7.53 2917 U9-Particulate

S9 6 5/30/2008 5/30/2008 50.2 54.9 6.79

Page 70sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 158132 dscfm 68 1 6.5 12.5 183.44 154056 dscfm 68 1 6.7 12.3 183.38 152787 dscfm 68 1 6.9 12.1 183.375 160871 dscfm 68 1 8.6 11.9 1 158247 dscfm 68 1 8.5 11.9 1 159571 dscfm 68 1 8.5 11.9 1

Page 71sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 0.993 Method 5 - Particulate Analysis(Coal Proximate and Ultimate analyses did not include any HAPs) Coal 50.8 38295 10.46 13687 0.993 Method 5 - Particulate Analysis(Coal Proximate and Ultimate analyses did not include any HAPs) Coal 51 38370 10.42 13717 0.993 Method 5 - Particulate Analysis(Coal Proximate and Ultimate analyses did not include any HAPs) Coal 50.9 38484 10.01 13701 0.983 Method 5 - Particulate Analysis(Coal Proximate and Ultimate analyses did not include any HAPs) Coal 50.3 38441 10.24 14187 0.983 Method 5 - Particulate Analysis(Coal Proximate and Ultimate analyses did not include any HAPs) Coal 50.2 38016 10.23 13880 0.983 Method 5 - Particulate Analysis(Coal Proximate and Ultimate analyses did not include any HAPs) Coal 50.2 37612 10.19 13772

Page 72sampling_runs

fuel_sulfur 3.6 3.79 4.81 3.21 3.69 3.91

Page 73sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 2917 U9-Particulate

S9 5 PM (Filterable) 0.00417 FALSE 2917 U9-Particulate

S9 6 PM (Filterable) 0.00365 FALSE 2917 U9-Particulate

S9 1 PM (Filterable) 0.00557 FALSE 2917 U9-Particulate

S9 2 PM (Filterable) 0.00542 FALSE 2917 U9-Particulate

S9 3 PM (Filterable) 0.00591 FALSE 2917 U9-Particulate

S9 4 PM (Filterable) 0.00344 FALSE

Page 74sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 5.65 pound per hour (lb/hr)

FALSE 0.01 pound per million British Thermal Unit (lb/MMBtu) FALSE Measurement Units for Concentration: gr/dscf 4.99 pound per hour (lb/hr)

FALSE 0.009 pound per million British Thermal Unit (lb/MMBtu) FALSE Measurement Units for Concentration: gr/dscf 7.55 pound per hour (lb/hr)

FALSE 0.012 pound per million British Thermal Unit (lb/MMBtu) FALSE Measurement Units for Concentration: gr/dscf 7.15 pound per hour (lb/hr)

FALSE 0.011 pound per million British Thermal Unit (lb/MMBtu) FALSE Measurement Units for Concentration: gr/dscf 7.74 pound per hour (lb/hr)

FALSE 0.013 pound per million British Thermal Unit (lb/MMBtu) FALSE Measurement Units for Concentration: gr/dscf 4.75 pound per hour (lb/hr)

FALSE 0.008 pound per million British Thermal Unit (lb/MMBtu) FALSE Measurement Units for Concentration: gr/dscf

Page 75sampling_run_pollutants1 run_pollutant_comment Measurement Units for Concentration: gr/dscf Measurement Units for Concentration: gr/dscf Measurement Units for Concentration: gr/dscf Measurement Units for Concentration: gr/dscf Measurement Units for Concentration: gr/dscf Measurement Units for Concentration: gr/dscf

Page 76sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 77sampling_run_fuel fuel_conc_MDL

Page 78