### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date 

## CPS Energy JT DEELY UNITS 1 AND 2

Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Friday, January 28, 2011 Page 1 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Facility Information: CPS Energy JT Deely Power Plant
9599 Gardner Rd.

San Antonio TX 78263 Contact: Mario Alvarez Phone: 210-353-5818 Fax: 210-353-4883 Email: maalvarez@cpsenergy.com Testing Company:
METCO Environmental
3226 Commander Dr.

Carrollton TX 75006 Contact: Ned Shappley Phone: 972-931-7127 Fax: 972-931-8398 Email: nshappley@metcoenv.com

Air Permit Number: 90267 Permitted Source ID/Name: JT Deely Units Number 1 and 2 Stack E-3 Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 110000464916 FRS #: 110000464916

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Pulverized Coal: Dry Bottom (Bituminous Coal)

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack Exit 312 4728 2832 4 312 16 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location Filterable Particulate OTM - 27/28 3 400 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Total Particulate OTM - 27/28 3 400 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit



### Friday, January 28, 2011 Page 2 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

Total PM2.5 OTM - 27/28 3 400 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Organic Condensible

Particulate OTM - 27/28 3 400 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 400 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Filterable PM2.5 OTM - 27/28 3 400 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Arsenic Method 29 3 240 0 Stack Exit Beryllium Method 29 3 240 0 Stack Exit Cadmium Method 29 3 240 0 Stack Exit Chromium Method 29 3 240 0 Stack Exit Lead Method 29 3 240 0 Stack Exit Manganese Method 29 3 240 0 Stack Exit Mercury Method 29 3 240 0 Stack Exit Nickel Method 29 3 240 0 Stack Exit Antimony Method 29 3 240 0 Stack Exit Filterable Particulate Method 29 3 240 0 Stack Exit Cobalt Method 29 0 Stack Exit Phosphorus (yellow or white) Method 29 0 Stack Exit Selenium Method 29 3 240 0 Stack Exit Co2 Method 3A CO2 3 400 0 Stack Exit O2 Method 3A O2 3 400 0 Stack Exit



### Friday, January 28, 2011 Page 3 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Sampling / Stack Data Results Summary



### Location Stack Exit - Method 29 Average Run Number 1 2 3
Test Date 4/20/2010 4/21/2010 4/22/2010 Run Start Time 11:20:00 AM 8:00:00 AM 7:40:00 AM

Run Finish Time 4:05:00 PM 12:40:00 PM 12:10:00 PM

Net Run Time, minutes 240 240 240 Dry Gas Meter Volume Sampled, dscf 169.022 168.113 168.836 168.657 Moisture Content of Stack Gas, % 12.31 12.70 12.87 12.627 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 14.3 14.7 14.7 14.567 Oxygen, % 5.1 4.9 4.8 4.933 Average Stack Gas Temperature, °F 316.90 318.35 326.81 320.687 Dry Volumetric Flow Rate, dry scfm 2,046,191.0 2,004,642.5 1,967,244.1 2,006,025.86 7 Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,535,031.5 3,505,724.2 3,499,034.5 3,513,263.40 0 Percent Isokinetic of Sampling Rate, % 92.8 94.2 96.4 94.467 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000
Fw 10640 10640 10640 10,640.000
Fc 1800 1800 1800 1,800.000



### Location Stack Exit - Method 3A CO2 Average Run Number
Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Friday, January 28, 2011 Page 4 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - Method 3A O2 Average Run Number
Test Date Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Stack Exit - OTM - 27/28 Average Run Number
Test Date Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Friday, January 28, 2011 Page 5 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Emissions Summary



### Location: Stack Exit - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.0114 0.0036 0.0061 0.007 lb/mmBtuO2 1.92E-06 6.03E-07 1.01E-06 0.000 

### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.00149 0.00098 0.00132 0.001 lb/mmBtuO2 2.51E-07 1.64E-07 2.19E-07 0.000 

### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.001 0.001 0.001 0.001 lb/mmBtuO2 1.69E-07 1.68E-07 1.66E-07 0.000 

### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.00116 0.00107 0.0015 0.001 lb/mmBtuO2 1.96E-07 1.79E-07 2.49E-07 0.000 

### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.01616 0.00516 0.00306 0.008 lb/mmBtuO2 2.73E-06 8.64E-07 5.07E-07 0.000 

### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.01 0.01 0.01 0.010 lb/mmBtuO2 1.69E-06 1.68E-06 1.66E-06 0.000 

### Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 17.3 9.3 7.7 11.433 lb/mmBtuO2 2.92E-03 1.56E-03 1.28E-03 0.002 

### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.003 0.00268 0.00259 0.003 lb/mmBtuO2 5.06E-07 4.49E-07 4.29E-07 0.000 

### Compound: Manganese Average



### Friday, January 28, 2011 Page 6 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

RunNumber 1 2 3 Mass_mg 0.00929 0.00492 0.0043 0.006 lb/mmBtuO2 1.57E-06 8.24E-07 7.13E-07 0.000 

### Compound: Mercury Average RunNumber 1 2 3 Mass_mg 0.03432 0.04605 0.03516 0.039 lb/mmBtuO2 5.79E-06 7.71E-06 5.83E-06 0.000 

### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 0.074 0.0348 0.0173 0.042 lb/mmBtuO2 1.25E-05 5.83E-06 2.87E-06 0.000 

### Compound: Phosphorus (yellow or white) Average RunNumber 1 2 3 Mass_mg 0.15045 0.12551 0.11774 0.131 lb/mmBtuO2 2.54E-05 2.10E-05 1.95E-05 0.000 

### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.0381 0.017 0.0137 0.023 lb/mmBtuO2 6.43E-06 2.85E-06 2.27E-06 0.000



### Location: Stack Exit - OTM - 27/28 Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 6.9 10.2 8.3 8.467 lb/mmBtuO2 1.62E-03 2.26E-03 1.87E-03 0.002 

### Compound: Filterable PM2.5 Average RunNumber 1 2 3 Mass_mg 0.8 1.4 1.7 1.300 lb/mmBtuO2 1.88E-04 3.10E-04 3.82E-04 0.000 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber 1 2 3 Mass_mg 12.8 16.1 26.2 18.367 lb/mmBtuO2 3.01E-03 3.57E-03 5.89E-03 0.004 

### Compound: Organic Condensible Particulate Average RunNumber 1 2 3 Mass_mg 5 9.9 3.8 6.233 lb/mmBtuO2 1.18E-03 2.19E-03 8.55E-04 0.001



### Friday, January 28, 2011 Page 7 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Process Run Data Compound: Total Particulate Average RunNumber 1 2 3 Mass_mg 23 34.2 36.3 31.167 lb/mmBtuO2 5.41E-03 7.58E-03 8.17E-03 0.007 

### Compound: Total PM2.5 Average RunNumber 1 2 3 Mass_mg 16.6 25.4 29.7 23.900 lb/mmBtuO2 3.91E-03 5.63E-03 6.68E-03 0.005



### Friday, January 28, 2011 Page 8 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Process Run Data



### Run Name Value UOM Comments Target Value 4 Coal Burned 1018 1000 Tons/hr Run 1 0


### 4 Average Heat Input 8380 MMBtu/hr Run 1 0
4 Steam Output 5971 1000 lb steam/hr Run 1 0
4 Flue Gas Oxygen Content 5.14 % Run 1 Collected by METCO Environmental 0

4 Flue Gas Carbon Dioxide Content 14.32 % Run 1 Collected by METCO Environmental 0



### 4 Flue Gas Moisture Content 12.18 % Run 1 Collected by METCO Environmental 0

4 Flue Gas Sampling Point Temperature 308 Deg F Run 1 Collected by METCO Environmental 0

4 Flue Gas Pressure 29.02 " Hg Run 1 Collected by METCO Environmental 0

4 Standard Pressure 29.92 "Hg Run 1 0
4 Standard Temperature 68 Deg F Run 1 0


### 4 Unit Gross Electrical Output 900 Mwe Run 1 0
4 Unit Net Electric Generation 856 MWh Run 1 0
5 Coal Burned 1013 1000 Tons/hr Run 2 0


### 5 Average Heat Input 8380 MMBtu/hr Run 2 0
5 Steam Output 5842 1000 lb steam/hr Run 2 0


### 5 Flue Gas Oxygen Content 4.86 % Run 2, collected my METCo Environmental 0

5 Flue Gas Carbon Dioxide Content 14.68 % Run 2, collected my METCo Environmental 0

5 Flue Gas Moisture Content 12.65 % Run 2, collected my METCo Environmental 0



### 5 Flue Gas Sampling Point Temperature 315 Deg F Run 2, collected my METCo Environmental 0

5 Flue Gas Pressure 28.87 " Hg Run 2, collected my METCo Environmental 0

5 Standard Pressure 68 "Hg Run 2 0



### Friday, January 28, 2011 Page 9 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

APCD Run Data

Process Lab Run Data 5 Standard Temperature 29.92 Deg F Run 2 0


### 5 Unit Gross Electrical Output 890 Mwe Run 2 0
5 Unit Net Electric Generation 846 MWh Run 2 0
6 Coal Burned 986 1000 Tons/hr Run 3 0


### 6 Average Heat Input 8380 MMBtu/hr Run 3 0
6 Steam Output 5747 1000 lb steam/hr Run 3 0
6 Flue Gas Oxygen Content 4.82 % Run 3 collected by METCO Environmental 0

6 Flue Gas Carbon Dioxide Content 14.73 % Run 3 collected by METCO Environmental 0



### 6 Flue Gas Moisture Content 11.56 % Run 3 collected by METCO Environmental 0

6 Flue Gas Sampling Point Temperature 323 Deg F Run 3 collected by METCO Environmental 0

6 Flue Gas Pressure 28.74 " Hg Run 3 collected by METCO Environmental 0

6 Standard Pressure 29.92 "Hg Run 3 0


### 6 Standard Temperature 68 Deg F Run 3 0
6 Unit Gross Electrical Output 874 Mwe Run 3 0
6 Unit Net Electric Generation 831 MWh Run 3 0

Run Name Value UOM Comments Target Value 

### 1 BAGHOUSE 0 0
1 OVERFIRE AIR 0 0



### Run Name Value UOM Comments 3 Fuel Higher Heating Value 11972 Btu/lb 

### 3 Fuel Moisture 30.53 % 3 Fuel Mercury Content 0.11 ppm 3 Fuel Cadmium Content 0.2 ppm 

### 3 Ultimate/Proximate Analysis 0 3 Fuel Nickel Content 5 ppm 3 Fuel Arsenic Content 1 ppm 3 Fuel Chromium Content 6 ppm



### Friday, January 28, 2011 Page 10 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

3 Fuel Beryllium Content 0.2 ppm 

### 3 Fuel Lead Content 3 ppm 3 Fuel Manganese Content 17 ppm 3 Fuel Chlorine Content 14 ppm 3 Fuel Fluorine Content 58 ppm 

### 3 Fuel Antimony Content 1 ppm 3 Fuel Selenium Content 1 ppm 4 Fuel Higher Heating Value 12705 Btu/lb 

### 4 Fuel Moisture 30.06 % 4 Fuel Mercury Content 0.13 ppm 4 Fuel Cadmium Content 0.2 ppm 4 Ultimate/Proximate Analysis 0 

### 4 Fuel Nickel Content 5 ppm 4 Fuel Arsenic Content 1 ppm 4 Fuel Chromium Content 6 ppm 

### 4 Fuel Beryllium Content 0.2 ppm 4 Fuel Lead Content 3 ppm 4 Fuel Manganese Content 14 ppm 4 Fuel Chlorine Content 12 ppm 

### 4 Fuel Fluorine Content 61 ppm 4 Fuel Antimony Content 1 ppm 4 Fuel Selenium Content 1 ppm 

### 5 Fuel Higher Heating Value 12021 Btu/lb 5 Fuel Moisture 29.86 % 5 Fuel Mercury Content 0.08 ppm 5 Fuel Cadmium Content 0.2 ppm 

### 5 Ultimate/Proximate Analysis 0 5 Fuel Nickel Content 4 ppm 5 Fuel Arsenic Content 1 ppm 

### 5 Fuel Chromium Content 5 ppm 5 Fuel Beryllium Content 0.2 ppm 5 Fuel Lead Content 2 ppm 5 Fuel Manganese Content 12 ppm 

### 5 Fuel Chlorine Content 11 ppm 5 Fuel Fluorine Content 61 ppm 5 Fuel Antimony Content 1 ppm 

### 5 Fuel Selenium Content 1 ppm

Friday, January 28, 2011 Page 11 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Sampling / Stack Data Results Detail



### Location Stack Exit - Method 29 Average Run Number 1 2 3 Test Date 4/20/2010 4/21/2010 4/22/2010 Run Start Time 11:20:00 AM 8:00:00 AM 7:40:00 AM Run Finish Time 4:05:00 PM 12:40:00 PM 12:10:00 PM Net Traversing Points 49 49 49 Net Run Time, minutes 240 240 240 Nozzle Diameter, inches 0.19 0.19 0.19 0.190 Pitot Tube Coefficient 0.82 0.82 0.82 0.820 Dry Gas Meter Calibration Factor 0.989 0.989 0.989 0.989 Barometric Pressure, inches of Mercury 29.22 29.11 28.97 29.100 Average Orifice Meter Differential, inches H2O 1.77 1.82 1.78 1.790 Dry Gas Meter Volume Sampled, cubic feet 178.223 178.037 180.259 178.840 Average Dry Gas Meter Temperature, °F 80.13 80.52 82.26 80.970 Dry Gas Meter Volume Sampled, dscf 169.022 168.113 168.836 168.657 Total Moisture Liquid collected, g 503.9 519.4 529.8 517.700 Volume of Water Vapor, standard cubic feet 23.72 24.45 24.94 24.370 Moisture Content of Stack Gas, % 12.31 12.70 12.87 12.627 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8769 0.873 0.8713 0.874 Carbon Dioxide, % 14.3 14.7 14.7 14.567 Oxygen, % 5.1 4.9 4.8 4.933 Carbon Monoxide & Nitrogen, % 80.6 80.4 80.5 80.500 Fuel Factor 1.10 1.09 1.10 Dry Molecular Weight, lb/lb-Mole 30.49 30.55 30.54 30.527 Wet Molecular weight, lb/lb-Mole 28.95 28.96 28.93 28.947 Flue Gas Static Pressure, inches of H2O -2.23 -2.95 -2.78 -2.653 Absolute Flue Gas Pressure, inches of Mercury 29.06 28.89 28.77 28.907 Average Stack Gas Temperature, °F 316.90 318.35 326.81 320.687 Average Velocity Head, inches of H2O 2.7134179382 2224 2.648928281

60154 2.597237226

31198 2.653
Average Stack Gas Velocity, feet/second 110.97 110.05 109.84 110.287 Stack Cross-Sectional Area, square feet 530.929 530.929 530.929 530.929 Dry Volumetric Flow Rate, dry scfm 2,046,191.0 2,004,642.5 1,967,244.1 2,006,025.8 67 Actual Wet Volumetric Flue Gas Flow Rate, acfm 3,535,031.5 3,505,724.2 3,499,034.5 3,513,263.4 00 Percent Isokinetic of Sampling Rate, % 92.8 94.2 96.4 94.467 Percent Excess Air, % 31.5 30.0 29.2 30.233 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Round Duct Diameter, inches 312 312 312 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Friday, January 28, 2011 Page 12 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - Method 3A CO2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, January 28, 2011 Page 13 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - Method 3A O2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, January 28, 2011 Page 14 of 15

### CPS Energy JT DEELY UNITS 1 AND 2

Location Stack Exit - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, January 28, 2011 Page 15 of 15