Name: Lois A. Knowlson

Title: Senior Environmental Engineer

Company: PSEG Fossil

Sign Date: 9/30/2010

Name: Anthony Fortunato

Title: Senior Test Engineer

Company: PSEG Maplewood Testing Services

Sign Date: 9/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

2411 PSEG Sewaren Unit 3

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 22, 2011 Page 1 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Facility Information:

2411 PSEG Sewaren Generating Station

751 Cliff Road

Sewaren NJ 07077

Contact: Joseph D. Krejsa

Phone: 732-750-2001

Fax:

Email: joseph.krejsa@pseg.com

Testing Company:

PSG Maplewood Testing Services

200 Boyden Avenue

Maplewood NJ 07040

Contact: Anthony Fortunato

Phone: 973-761-1005

Fax:

Email: anthony.fortunato2@pseg.com

Air Permit Number:

2411-NJDEP PI 18068, BOP 080001

Permitted Source ID/Name:

U3 3

Permitted Maximum Process Rate:

1600 MMBtu/hr

Max. Normal Operation Process Rate:

1600 MMBtu/hr

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

External combustion, electric generating unit, tangentially fired, combusting natural gas or #6 fuel oil; no control 

equipment

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000869150 FRS #: 110000801614

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Tangential Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 14.263 151.7 151.7 14.263 487 1579 4 4

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Regulation Description Compound Limit Unit

NJAC 7:27-4.2(a) Particulate 160 lb/hr

NJAC 7:27-16.8(b)1 Volatile Organic 

Compounds (total)

50 ppm corrected

NJAC 7:27-16.8(b)2 Carbon Monoxide 100 ppm corrected

Tuesday, February 22, 2011 Page 2 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Stack Exit Filterable PM2.5 OTM - 27/28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit OTM - 27/28 3 240 0

Stack Exit Filterable Particulate OTM - 27/28 3 240 0

Stack Exit Total PM2.5 OTM - 27/28 3 240 0

Stack Exit Total Particulate OTM - 27/28 3 240 0

Tuesday, February 22, 2011 Page 3 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

Organic Condensible 

Particulate

Stack Exit OTM - 27/28 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cobalt Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit O2 Method 3A O2 3 120 0

Stack Exit Co2 Method 3A CO2 3 120 0

Organic Condensible 

Particulate

Stack Exit Method 5/OTM-28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit Method 5/OTM-28 3 240 0

Stack Exit Total Particulate Method 5/OTM-28 3 240 0

Stack Exit Filterable Particulate Method 5/OTM-28 3 240 0

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Tuesday, February 22, 2011 Page 4 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:48:00 PM 9:06:00 AM

Run Finish Time 6:45:00 PM 9:57:00 PM 11:14:00 AM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 72.623 73.962 76.282 74.289

Moisture Content of Stack Gas, % 8.31 8.74 8.24 8.430

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Average Stack Gas Temperature, °F 258.92 256.92 260.50 258.780

Dry Volumetric Flow Rate, dry scfm 388,522.3 399,899.8 400,014.1 396,145.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 576,953.3 594,788.3 595,267.7 589,003.100

Percent Isokinetic of Sampling Rate, % 96.9 95.9 97.1 96.633

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 10

Average

Run Number 1-1 1-2 1-3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:45:00 PM 9:15:00 AM

Run Finish Time 6:47:00 PM 10:01:00 

PM

11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5 394,229.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.85 9.02 8.07 8.647

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 5 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 7/7/2010 7/8/2010 7/9/2010

Run Start Time 7:04:00 AM 7:28:00 

AM

12:58:00 PM

Run Finish Time 9:10:00 PM 11:10:00 

PM

9:06:00 PM

Net Run Time, minutes 576 480 480

Dry Gas Meter Volume Sampled, dscf 335.816 397.942 316.423 350.060

Moisture Content of Stack Gas, % 6.75 7.08 6.70 6.843

Moisture Saturation at Stack Gas Temperature, % 97.13 100.00 93.65 96.927

Carbon Dioxide, % 5.3 6.4 5.1 5.600

Oxygen, % 13.9 12.5 13.8 13.400

Average Stack Gas Temperature, °F 210.54 233.54 208.54 217.540

Dry Volumetric Flow Rate, dry scfm 208,194.9 312,709.2 198,306.1 239,736.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 283,538.5 441,752.3 270,114.2 331,801.667

Percent Isokinetic of Sampling Rate, % 98.9 93.7 97.5 96.700

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 25A

Average

Run Number 1-1 1-2 1-3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:45:00 PM 9:15:00 AM

Run Finish Time 6:47:00 PM 10:01:00 

PM

11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5 394,229.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.31 8.94 8.24 8.497

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 6 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 7/9/2010 7/9/2010 7/9/2010

Run Start Time 12:58:00 PM 2:40:00 PM 4:10:00 PM

Run Finish Time 2:07:00 PM 3:51:00 PM 5:17:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 39.915 38.939 38.797 39.217

Moisture Content of Stack Gas, % 9.81 9.67 9.30 9.593

Moisture Saturation at Stack Gas Temperature, % 92.57 88.94 88.27 89.927

Carbon Dioxide, % 5.162 5.198 5.185 5.182

Oxygen, % 13.841 13.918 13.929 13.896

Average Stack Gas Temperature, °F 208.00 205.96 205.54 206.500

Dry Volumetric Flow Rate, dry scfm 194,364.8 185,497.1 186,049.5 188,637.133

Actual Wet Volumetric Flue Gas Flow Rate, acfm 273,470.3 260,142.0 259,950.2 264,520.833

Percent Isokinetic of Sampling Rate, % 99.2 101.4 100.7 100.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 7/6/2010 7/7/2010 7/8/2010

Run Start Time 3:58:00 PM 1:00:00 PM 8:30:00 AM

Run Finish Time 9:27:00 PM 6:33:00 PM 2:07:00 PM

Net Run Time, minutes 300 300 300

Dry Gas Meter Volume Sampled, dscf 168.639 181.447 171.485 173.857

Moisture Content of Stack Gas, % 8.38 7.90 8.13 8.137

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 8.5 7.3 7.5 7.767

Oxygen, % 9.8 11 10.8 10.533

Average Stack Gas Temperature, °F 294.96 271.29 259.42 275.223

Dry Volumetric Flow Rate, dry scfm 365,334.1 392,195.1 369,489.4 375,672.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 571,871.3 590,185.7 547,995.3 570,017.433

Percent Isokinetic of Sampling Rate, % 99.4 97.8 99.0 98.733

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 7 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 6C

Average

Run Number 1-1 1-2 1-3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:45:00 PM 9:15:00 AM

Run Finish Time 6:47:00 PM 10:01:00 

PM

11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5 394,229.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.85 9.02 8.07 8.647

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - Method 6C 3

Average

Run Number 3-1 3-2 3-3

Test Date 7/9/2010 7/9/2010 7/9/2010

Run Start Time 12:59:00 PM 2:42:00 PM 4:12:00 PM

Run Finish Time 2:09:00 PM 3:42:00 PM 5:11:00 PM

Carbon Dioxide, % 5.162 5.198 5.185 5.182

Oxygen, % 13.841 13.918 13.929 13.896

Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775 190,654.633

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.5 5.5 5.5 5.500

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 8 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 7E

Average

Run Number 3-1 3-2 3-3

Test Date 7/9/2010 7/9/2010 7/9/2010

Run Start Time 12:59:00 PM 2:42:00 PM 4:12:00 PM

Run Finish Time 2:09:00 PM 3:42:00 PM 5:11:00 PM

Carbon Dioxide, % 5.162 5.198 5.185 5.182

Oxygen, % 13.841 13.918 13.929 13.896

Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775 190,654.633

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.5 5.5 5.5 5.500

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 7/6/2010 7/7/2010 7/8/2010

Run Start Time 4:00:00 PM 1:00:00 PM 8:30:00 AM

Run Finish Time 10:05:00 PM 7:08:00 PM 2:17:00 PM

Net Run Time, minutes 338.77 347.94 330.31

Dry Gas Meter Volume Sampled, dscf 122.581 127.693 123.265 124.513

Moisture Content of Stack Gas, % 8.35 7.98 8.43 8.253

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 8.5 7.3 7.5 7.767

Oxygen, % 9.8 11 10.8 10.533

Average Stack Gas Temperature, °F 292.50 267.42 257.25 272.390

Dry Volumetric Flow Rate, dry scfm 379,267.3 398,296.6 379,666.7 385,743.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 590,761.0 596,514.3 562,666.1 583,313.800

Percent Isokinetic of Sampling Rate, % 96.7 92.3 98.5 95.833

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 9 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Emissions Summary

Location: Stack Exit - Method 0011

Compound: Formaldehyde

Average

RunNumber 1 2 3

Mass_mg 0.28 0.24 0.11 0.210

lb/mmBtuO2 1.60E-04 1.36E-04 6.17E-05 0.000

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1-1 1-2 1-3

Elb/hr 1.23E+00 1.23E+00 0.00E+00 0.820

gr/dscf 3.69E-04 3.64E-04 0.00E+00 0.000

lb/mmBtuO2 9.92E-04 9.90E-04 0.00E+00 0.001

mg/dscm 8.44E-01 8.34E-01 0.00E+00 0.559

ppm 7.25E-01 7.16E-01 0.00E+00 0.480

ppm@7%O2 9.88E-01 9.85E-01 0.00E+00 0.658

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000019 0.0000000035 0.0000000017 0.000

Elb/hr 1.56E-10 3.64E-10 1.41E-10 0.000

gr/dscf 8.73E-14 1.36E-13 8.29E-14 0.000

lb/mmBtuO2 3.42E-13 4.43E-13 3.20E-13 0.000

mg/dscm 2.00E-10 3.11E-10 1.90E-10 0.000

ng/dscm 2.00E-04 3.11E-04 1.90E-04 0.000

ng/dscm@7%O2 3.97E-04 5.15E-04 3.72E-04 0.000

ppm 1.13E-11 1.76E-11 1.07E-11 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000021 0.0000000029 0.0000000019 0.000

Elb/hr 1.72E-10 3.01E-10 1.58E-10 0.000

gr/dscf 9.65E-14 1.12E-13 9.27E-14 0.000

lb/mmBtuO2 3.78E-13 3.67E-13 3.58E-13 0.000

mg/dscm 2.21E-10 2.57E-10 2.12E-10 0.000

ng/dscm 2.21E-04 2.57E-04 2.12E-04 0.000

ng/dscm@7%O2 4.39E-04 4.25E-04 4.15E-04 0.000

ppm 1.30E-11 1.51E-11 1.25E-11 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000018 0.0000000034 0.0000000018 0.000

Elb/hr 1.48E-10 3.53E-10 1.49E-10 0.000

gr/dscf 8.27E-14 1.32E-13 8.78E-14 0.000

lb/mmBtuO2 3.24E-13 4.31E-13 3.39E-13 0.000

Tuesday, February 22, 2011 Page 10 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

mg/dscm 1.89E-10 3.02E-10 2.01E-10 0.000

ng/dscm 1.89E-04 3.02E-04 2.01E-04 0.000

ng/dscm@7%O2 3.75E-04 5.00E-04 3.94E-04 0.000

ppm 1.11E-11 1.77E-11 1.18E-11 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000018 0.0000000039 0.0000000017 0.000

Elb/hr 1.48E-10 4.05E-10 1.41E-10 0.000

gr/dscf 8.27E-14 1.51E-13 8.29E-14 0.000

lb/mmBtuO2 3.24E-13 4.94E-13 3.20E-13 0.000

mg/dscm 1.89E-10 3.46E-10 1.90E-10 0.000

ng/dscm 1.89E-04 3.46E-04 1.90E-04 0.000

ng/dscm@7%O2 3.75E-04 5.73E-04 3.72E-04 0.000

ppm 1.16E-11 2.13E-11 1.17E-11 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000015 0.0000000037 0.0000000015 0.000

Elb/hr 1.23E-10 3.85E-10 1.24E-10 0.000

gr/dscf 6.89E-14 1.43E-13 7.32E-14 0.000

lb/mmBtuO2 2.70E-13 4.69E-13 2.83E-13 0.000

mg/dscm 1.58E-10 3.28E-10 1.67E-10 0.000

ng/dscm 1.58E-04 3.28E-04 1.67E-04 0.000

ng/dscm@7%O2 3.14E-04 5.43E-04 3.27E-04 0.000

ppm 1.01E-11 2.11E-11 1.07E-11 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000019 0.0000000042 0.0000000018 0.000

Elb/hr 1.56E-10 4.37E-10 1.49E-10 0.000

gr/dscf 8.73E-14 1.63E-13 8.78E-14 0.000

lb/mmBtuO2 3.42E-13 5.32E-13 3.39E-13 0.000

mg/dscm 2.00E-10 3.73E-10 2.01E-10 0.000

ng/dscm 2.00E-04 3.73E-04 2.01E-04 0.000

ng/dscm@7%O2 3.97E-04 6.17E-04 3.94E-04 0.000

ppm 1.23E-11 2.29E-11 1.24E-11 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000014 0.0000000036 0.0000000015 0.000

Elb/hr 1.15E-10 3.74E-10 1.24E-10 0.000

gr/dscf 6.43E-14 1.40E-13 7.32E-14 0.000

lb/mmBtuO2 2.52E-13 4.56E-13 2.83E-13 0.000

mg/dscm 1.47E-10 3.20E-10 1.67E-10 0.000

ng/dscm 1.47E-04 3.20E-04 1.67E-04 0.000

ng/dscm@7%O2 2.92E-04 5.30E-04 3.27E-04 0.000

ppm 9.45E-12 2.05E-11 1.07E-11 0.000

Tuesday, February 22, 2011 Page 11 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000018 0.0000000038 0.0000000017 0.000

Elb/hr 1.48E-10 3.95E-10 1.41E-10 0.000

gr/dscf 8.27E-14 1.47E-13 8.29E-14 0.000

lb/mmBtuO2 3.24E-13 4.81E-13 3.20E-13 0.000

mg/dscm 1.89E-10 3.37E-10 1.90E-10 0.000

ng/dscm 1.89E-04 3.37E-04 1.90E-04 0.000

ng/dscm@7%O2 3.75E-04 5.58E-04 3.72E-04 0.000

ppm 1.16E-11 2.08E-11 1.17E-11 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.0000000044 0.0000000018 0.000

Elb/hr 1.39E-10 4.57E-10 1.49E-10 0.000

gr/dscf 7.81E-14 1.71E-13 8.78E-14 0.000

lb/mmBtuO2 3.06E-13 5.57E-13 3.39E-13 0.000

mg/dscm 1.79E-10 3.91E-10 2.01E-10 0.000

ng/dscm 1.79E-04 3.91E-04 2.01E-04 0.000

ng/dscm@7%O2 3.55E-04 6.47E-04 3.94E-04 0.000

ppm 1.15E-11 2.51E-11 1.29E-11 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.0000000044 0.0000000018 0.000

Elb/hr 1.39E-10 4.57E-10 1.49E-10 0.000

gr/dscf 7.81E-14 1.71E-13 8.78E-14 0.000

lb/mmBtuO2 3.06E-13 5.57E-13 3.39E-13 0.000

mg/dscm 1.79E-10 3.91E-10 2.01E-10 0.000

ng/dscm 1.79E-04 3.91E-04 2.01E-04 0.000

ng/dscm@7%O2 3.55E-04 6.47E-04 3.94E-04 0.000

ppm 1.21E-11 2.63E-11 1.36E-11 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000018 0.0000000063 0.0000000019 0.000

Elb/hr 1.48E-10 6.55E-10 1.58E-10 0.000

gr/dscf 8.27E-14 2.44E-13 9.27E-14 0.000

lb/mmBtuO2 3.24E-13 7.98E-13 3.58E-13 0.000

mg/dscm 1.89E-10 5.59E-10 2.12E-10 0.000

ng/dscm 1.89E-04 5.59E-04 2.12E-04 0.000

ng/dscm@7%O2 3.75E-04 9.25E-04 4.15E-04 0.001

ppm 1.34E-11 3.95E-11 1.50E-11 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000047 0.0000000093 0.0000000052 0.000

Elb/hr 3.85E-10 9.67E-10 4.31E-10 0.000

Tuesday, February 22, 2011 Page 12 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

gr/dscf 2.16E-13 3.61E-13 2.54E-13 0.000

lb/mmBtuO2 8.47E-13 1.18E-12 9.80E-13 0.000

mg/dscm 4.94E-10 8.25E-10 5.80E-10 0.000

ng/dscm 4.94E-04 8.25E-04 5.80E-04 0.001

ng/dscm@7%O2 9.81E-04 1.37E-03 1.14E-03 0.001

ppm 3.00E-11 5.01E-11 3.52E-11 0.000

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000086 0.00000015 0.00000012 0.000

Elb/hr 7.05E-09 1.56E-08 9.95E-09 0.000

gr/dscf 3.95E-12 5.82E-12 5.85E-12 0.000

lb/mmBtuO2 1.55E-11 1.90E-11 2.26E-11 0.000

mg/dscm 9.05E-09 1.33E-08 1.34E-08 0.000

ng/dscm 9.05E-03 1.33E-02 1.34E-02 0.012

ng/dscm@7%O2 1.80E-02 2.20E-02 2.62E-02 0.022

ppm 0.000

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000048 0.00000073 0.00000062 0.000

Elb/hr 3.94E-08 7.59E-08 5.14E-08 0.000

gr/dscf 2.21E-11 2.83E-11 3.02E-11 0.000

lb/mmBtuO2 8.65E-11 9.25E-11 1.17E-10 0.000

mg/dscm 5.05E-08 6.48E-08 6.92E-08 0.000

ng/dscm 5.05E-02 6.48E-02 6.92E-02 0.062

ng/dscm@7%O2 1.00E-01 1.07E-01 1.35E-01 0.114

ppm 0.000

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000034 0.000000054 0.000000048 0.000

Elb/hr 2.79E-09 5.61E-09 3.98E-09 0.000

gr/dscf 1.56E-12 2.09E-12 2.34E-12 0.000

lb/mmBtuO2 6.12E-12 6.84E-12 9.05E-12 0.000

mg/dscm 3.58E-09 4.79E-09 5.36E-09 0.000

ng/dscm 3.58E-03 4.79E-03 5.36E-03 0.005

ng/dscm@7%O2 7.11E-03 7.93E-03 1.05E-02 0.009

ppm 2.38E-10 3.19E-10 3.57E-10 0.000

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000037 0.000000038 0.000000044 0.000

Elb/hr 3.03E-09 3.95E-09 3.65E-09 0.000

gr/dscf 1.70E-12 1.47E-12 2.15E-12 0.000

lb/mmBtuO2 6.66E-12 4.81E-12 8.29E-12 0.000

mg/dscm 3.89E-09 3.37E-09 4.91E-09 0.000

ng/dscm 3.89E-03 3.37E-03 4.91E-03 0.004

ng/dscm@7%O2 7.72E-03 5.58E-03 9.61E-03 0.008

ppm 0.000

Tuesday, February 22, 2011 Page 13 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.0000015 0.0000021 0.0000019 0.000

Elb/hr 1.23E-07 2.18E-07 1.58E-07 0.000

gr/dscf 6.89E-11 8.14E-11 9.27E-11 0.000

lb/mmBtuO2 2.70E-10 2.66E-10 3.58E-10 0.000

mg/dscm 1.58E-07 1.86E-07 2.12E-07 0.000

ng/dscm 1.58E-01 1.86E-01 2.12E-01 0.185

ng/dscm@7%O2 3.14E-01 3.08E-01 4.15E-01 0.346

ppm 0.000

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000021 0.000000028 0.000000027 0.000

Elb/hr 1.72E-09 2.91E-09 2.24E-09 0.000

gr/dscf 9.65E-13 1.09E-12 1.32E-12 0.000

lb/mmBtuO2 3.78E-12 3.55E-12 5.09E-12 0.000

mg/dscm 2.21E-09 2.49E-09 3.01E-09 0.000

ng/dscm 2.21E-03 2.49E-03 3.01E-03 0.003

ng/dscm@7%O2 4.39E-03 4.12E-03 5.89E-03 0.005

ppm 0.000

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.0000000042 0.0000000017 0.000

Elb/hr 1.39E-10 4.37E-10 1.41E-10 0.000

gr/dscf 7.81E-14 1.63E-13 8.29E-14 0.000

lb/mmBtuO2 3.06E-13 5.32E-13 3.20E-13 0.000

mg/dscm 1.79E-10 3.73E-10 1.90E-10 0.000

ng/dscm 1.79E-04 3.73E-04 1.90E-04 0.000

ng/dscm@7%O2 3.55E-04 6.17E-04 3.72E-04 0.000

ppm 1.15E-11 2.39E-11 1.22E-11 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000022 0.000000006 0.0000000018 0.000

Elb/hr 1.80E-10 6.24E-10 1.49E-10 0.000

gr/dscf 1.01E-13 2.33E-13 8.78E-14 0.000

lb/mmBtuO2 3.96E-13 7.60E-13 3.39E-13 0.000

mg/dscm 2.31E-10 5.33E-10 2.01E-10 0.000

ng/dscm 2.31E-04 5.33E-04 2.01E-04 0.000

ng/dscm@7%O2 4.59E-04 8.82E-04 3.94E-04 0.001

ppm 1.63E-11 3.76E-11 1.42E-11 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000021 0.0000000057 0.000000002 0.000

Elb/hr 1.72E-10 5.92E-10 1.66E-10 0.000

Tuesday, February 22, 2011 Page 14 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

gr/dscf 9.65E-14 2.21E-13 9.75E-14 0.000

lb/mmBtuO2 3.78E-13 7.22E-13 3.77E-13 0.000

mg/dscm 2.21E-10 5.06E-10 2.23E-10 0.000

ng/dscm 2.21E-04 5.06E-04 2.23E-04 0.000

ng/dscm@7%O2 4.39E-04 8.37E-04 4.37E-04 0.001

ppm 1.65E-11 3.78E-11 1.67E-11 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000057 0.0000000048 0.0000000024 0.000

Elb/hr 4.67E-10 4.99E-10 1.99E-10 0.000

gr/dscf 2.62E-13 1.86E-13 1.17E-13 0.000

lb/mmBtuO2 1.03E-12 6.08E-13 4.52E-13 0.000

mg/dscm 6.00E-10 4.26E-10 2.68E-10 0.000

ng/dscm 6.00E-04 4.26E-04 2.68E-04 0.000

ng/dscm@7%O2 1.19E-03 7.05E-04 5.25E-04 0.001

ppm 4.71E-11 3.35E-11 2.11E-11 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.000000003 0.0000000058 0.0000000051 0.000

Elb/hr 2.46E-10 6.03E-10 4.23E-10 0.000

gr/dscf 1.38E-13 2.25E-13 2.49E-13 0.000

lb/mmBtuO2 5.40E-13 7.35E-13 9.61E-13 0.000

mg/dscm 3.16E-10 5.15E-10 5.69E-10 0.000

ng/dscm 3.16E-04 5.15E-04 5.69E-04 0.000

ng/dscm@7%O2 6.27E-04 8.52E-04 1.11E-03 0.001

ppm 0.000

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.000000004 0.0000000045 0.0000000066 0.000

Elb/hr 3.28E-10 4.68E-10 5.47E-10 0.000

gr/dscf 1.84E-13 1.75E-13 3.22E-13 0.000

lb/mmBtuO2 7.21E-13 5.70E-13 1.24E-12 0.000

mg/dscm 4.21E-10 3.99E-10 7.37E-10 0.000

ng/dscm 4.21E-04 3.99E-04 7.37E-04 0.001

ng/dscm@7%O2 8.36E-04 6.60E-04 1.44E-03 0.001

ppm 0.000

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000083 0.00000017 0.000000097 0.000

Elb/hr 6.81E-09 1.77E-08 8.04E-09 0.000

gr/dscf 3.81E-12 6.59E-12 4.73E-12 0.000

lb/mmBtuO2 1.50E-11 2.15E-11 1.83E-11 0.000

mg/dscm 8.73E-09 1.51E-08 1.08E-08 0.000

ng/dscm 8.73E-03 1.51E-02 1.08E-02 0.012

ng/dscm@7%O2 1.73E-02 2.50E-02 2.11E-02 0.021

ppm 0.000

Tuesday, February 22, 2011 Page 15 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000000026 0.0000000072 0.0000000034 0.000

Elb/hr 2.13E-10 7.48E-10 2.82E-10 0.000

gr/dscf 1.19E-13 2.79E-13 1.66E-13 0.000

lb/mmBtuO2 4.68E-13 9.12E-13 6.41E-13 0.000

mg/dscm 2.73E-10 6.39E-10 3.80E-10 0.000

ng/dscm 2.73E-04 6.39E-04 3.80E-04 0.000

ng/dscm@7%O2 5.42E-04 1.06E-03 7.44E-04 0.001

ppm 0.000

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000012 0.0000000133 0.0000000093 0.000

Elb/hr 9.84E-10 1.38E-09 7.71E-10 0.000

gr/dscf 5.51E-13 5.16E-13 4.54E-13 0.000

lb/mmBtuO2 2.16E-12 1.68E-12 1.75E-12 0.000

mg/dscm 1.26E-09 1.18E-09 1.04E-09 0.000

ng/dscm 1.26E-03 1.18E-03 1.04E-03 0.001

ng/dscm@7%O2 2.50E-03 1.95E-03 2.04E-03 0.002

ppm 6.60E-11 6.17E-11 5.43E-11 0.000

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000081 0.0000000034 0.000

Elb/hr 2.62E-10 8.42E-10 2.82E-10 0.000

gr/dscf 1.47E-13 3.14E-13 1.66E-13 0.000

lb/mmBtuO2 5.76E-13 1.03E-12 6.41E-13 0.000

mg/dscm 3.37E-10 7.19E-10 3.80E-10 0.000

ng/dscm 3.37E-04 7.19E-04 3.80E-04 0.000

ng/dscm@7%O2 6.69E-04 1.19E-03 7.44E-04 0.001

ppm 1.82E-11 3.90E-11 2.06E-11 0.000

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000019 0.0000000035 0.0000000017 0.000

Elb/hr 1.56E-10 3.64E-10 1.41E-10 0.000

gr/dscf 8.73E-14 1.36E-13 8.29E-14 0.000

lb/mmBtuO2 3.42E-13 4.43E-13 3.20E-13 0.000

mg/dscm 2.00E-10 3.11E-10 1.90E-10 0.000

ng/dscm 2.00E-04 3.11E-04 1.90E-04 0.000

ng/dscm@7%O2 3.97E-04 5.15E-04 3.72E-04 0.000

ppm 1.13E-11 1.76E-11 1.07E-11 0.000

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000022 0.0000000031 0.000000002 0.000

Elb/hr 1.80E-10 3.22E-10 1.66E-10 0.000

Tuesday, February 22, 2011 Page 16 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

gr/dscf 1.01E-13 1.20E-13 9.75E-14 0.000

lb/mmBtuO2 3.96E-13 3.93E-13 3.77E-13 0.000

mg/dscm 2.31E-10 2.75E-10 2.23E-10 0.000

ng/dscm 2.31E-04 2.75E-04 2.23E-04 0.000

ng/dscm@7%O2 4.59E-04 4.55E-04 4.37E-04 0.000

ppm 1.36E-11 1.62E-11 1.31E-11 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000067 0.0000000098 0.000000011 0.000

Elb/hr 5.49E-10 1.02E-09 9.12E-10 0.000

gr/dscf 3.08E-13 3.80E-13 5.36E-13 0.000

lb/mmBtuO2 1.21E-12 1.24E-12 2.07E-12 0.000

mg/dscm 7.05E-10 8.70E-10 1.23E-09 0.000

ng/dscm 7.05E-04 8.70E-04 1.23E-03 0.001

ng/dscm@7%O2 1.40E-03 1.44E-03 2.41E-03 0.002

ppm 4.34E-11 5.35E-11 7.55E-11 0.000

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000016 0.0000000039 0.0000000016 0.000

Elb/hr 1.31E-10 4.05E-10 1.33E-10 0.000

gr/dscf 7.35E-14 1.51E-13 7.80E-14 0.000

lb/mmBtuO2 2.88E-13 4.94E-13 3.02E-13 0.000

mg/dscm 1.68E-10 3.46E-10 1.79E-10 0.000

ng/dscm 1.68E-04 3.46E-04 1.79E-04 0.000

ng/dscm@7%O2 3.34E-04 5.73E-04 3.50E-04 0.000

ppm 1.08E-11 2.22E-11 1.15E-11 0.000

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000021 0.0000000044 0.000000003 0.000

Elb/hr 1.72E-10 4.57E-10 2.49E-10 0.000

gr/dscf 9.65E-14 1.71E-13 1.46E-13 0.000

lb/mmBtuO2 3.78E-13 5.57E-13 5.65E-13 0.000

mg/dscm 2.21E-10 3.91E-10 3.35E-10 0.000

ng/dscm 2.21E-04 3.91E-04 3.35E-04 0.000

ng/dscm@7%O2 4.39E-04 6.47E-04 6.56E-04 0.001

ppm 1.49E-11 2.63E-11 2.26E-11 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000022 0.000000035 0.0000000069 0.000

Elb/hr 1.80E-10 3.64E-09 5.72E-10 0.000

gr/dscf 1.01E-13 1.36E-12 3.37E-13 0.000

lb/mmBtuO2 3.96E-13 4.43E-12 1.30E-12 0.000

mg/dscm 2.31E-10 3.11E-09 7.70E-10 0.000

ng/dscm 2.31E-04 3.11E-03 7.70E-04 0.001

ng/dscm@7%O2 4.59E-04 5.15E-03 1.51E-03 0.002

ppm 1.63E-11 2.19E-10 5.44E-11 0.000

Tuesday, February 22, 2011 Page 17 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000057 0.0000000027 0.000

Elb/hr 2.62E-10 5.92E-10 2.24E-10 0.000

gr/dscf 1.47E-13 2.21E-13 1.32E-13 0.000

lb/mmBtuO2 5.76E-13 7.22E-13 5.09E-13 0.000

mg/dscm 3.37E-10 5.06E-10 3.01E-10 0.000

ng/dscm 3.37E-04 5.06E-04 3.01E-04 0.000

ng/dscm@7%O2 6.69E-04 8.37E-04 5.89E-04 0.001

ppm 2.51E-11 3.78E-11 2.25E-11 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000087 0.0000000048 0.0000000024 0.000

Elb/hr 7.13E-10 4.99E-10 1.99E-10 0.000

gr/dscf 4.00E-13 1.86E-13 1.17E-13 0.000

lb/mmBtuO2 1.57E-12 6.08E-13 4.52E-13 0.000

mg/dscm 9.15E-10 4.26E-10 2.68E-10 0.000

ng/dscm 9.15E-04 4.26E-04 2.68E-04 0.001

ng/dscm@7%O2 1.82E-03 7.05E-04 5.25E-04 0.001

ppm 7.19E-11 3.35E-11 2.11E-11 0.000

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.0000000371 0.0000000622 0.0000000408 0.000

Elb/hr 3.04E-09 6.47E-09 3.38E-09 0.000

gr/dscf 1.70E-12 2.41E-12 1.99E-12 0.000

lb/mmBtuO2 6.68E-12 7.88E-12 7.69E-12 0.000

mg/dscm 3.90E-09 5.52E-09 4.55E-09 0.000

ng/dscm 3.90E-03 5.52E-03 4.55E-03 0.005

ng/dscm@7%O2 7.74E-03 9.13E-03 8.91E-03 0.009

ppm 0.000

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.0000000378 0.0000000942 0.0000000302 0.000

Elb/hr 3.10E-09 9.79E-09 2.50E-09 0.000

gr/dscf 1.74E-12 3.65E-12 1.47E-12 0.000

lb/mmBtuO2 6.81E-12 1.19E-11 5.69E-12 0.000

mg/dscm 3.98E-09 8.36E-09 3.37E-09 0.000

ng/dscm 3.98E-03 8.36E-03 3.37E-03 0.005

ng/dscm@7%O2 7.90E-03 1.38E-02 6.60E-03 0.009

ppm 0.000

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1-1 1-2 1-3

Elb/hr 1.12E+00 8.43E-01 2.50E-01 0.738

Tuesday, February 22, 2011 Page 18 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

gr/dscf 3.35E-04 2.50E-04 7.29E-05 0.000

lb/mmBtuO2 9.01E-04 6.78E-04 2.02E-04 0.001

mg/dscm 7.66E-01 5.71E-01 1.67E-01 0.501

ppm 4.18E-01 3.12E-01 9.10E-02 0.274

ppm@7%O2 5.70E-01 4.29E-01 1.28E-01 0.376

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 1 0.99 0.82 0.937

Elb/hr 6.44E-01 6.24E-01 5.20E-01 0.596

lb/mmBtuO2 1.50E-03 1.54E-03 1.28E-03 0.001

mg/dscm 8.85E-01 8.98E-01 7.47E-01 0.843

mg/dscm@7%O2 1.74E+00 1.79E+00 1.49E+00 1.673

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.11 0.11 0.11 0.110

Elb/hr 7.09E-02 6.93E-02 6.98E-02 0.070

lb/mmBtuO2 1.65E-04 1.71E-04 1.72E-04 0.000

mg/dscm 9.73E-02 9.98E-02 1.00E-01 0.099

mg/dscm@7%O2 1.92E-01 1.99E-01 1.99E-01 0.197

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.3452 0.3122 0.29153 0.316

Elb/hr 9.89E-02 8.93E-02 8.31E-02 0.090

lb/mmBtuO2 7.81E-05 7.36E-05 7.13E-05 0.000

mg/dscm 7.23E-02 6.08E-02 6.00E-02 0.064

mg/dscm@7%O2 9.05E-02 8.54E-02 8.26E-02 0.086

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.0209 0.0177 0.00964 0.016

Elb/hr 5.99E-03 5.06E-03 2.75E-03 0.005

lb/mmBtuO2 4.73E-06 4.17E-06 2.36E-06 0.000

mg/dscm 4.38E-03 3.45E-03 1.99E-03 0.003

mg/dscm@7%O2 5.48E-03 4.84E-03 2.74E-03 0.004

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00267 0.00241 0.00215 0.002

Elb/hr 7.65E-04 6.89E-04 6.13E-04 0.001

lb/mmBtuO2 6.04E-07 5.68E-07 5.26E-07 0.000

mg/dscm 5.59E-04 4.69E-04 4.43E-04 0.000

mg/dscm@7%O2 7.00E-04 6.58E-04 6.10E-04 0.001

Tuesday, February 22, 2011 Page 19 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00045 0.00043 0.000294 0.000

Elb/hr 1.29E-04 1.23E-04 8.38E-05 0.000

lb/mmBtuO2 1.02E-07 1.01E-07 7.19E-08 0.000

mg/dscm 9.42E-05 8.37E-05 6.06E-05 0.000

mg/dscm@7%O2 1.18E-04 1.18E-04 8.34E-05 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.07089 0.06335 0.02282 0.052

Elb/hr 2.03E-02 1.81E-02 6.50E-03 0.015

lb/mmBtuO2 1.60E-05 1.49E-05 5.58E-06 0.000

mg/dscm 1.48E-02 1.23E-02 4.70E-03 0.011

mg/dscm@7%O2 1.85E-02 1.73E-02 6.47E-03 0.014

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.20106 0.19105 0.15928 0.184

Elb/hr 5.76E-02 5.46E-02 4.54E-02 0.053

lb/mmBtuO2 4.55E-05 4.50E-05 3.89E-05 0.000

mg/dscm 4.21E-02 3.72E-02 3.28E-02 0.037

mg/dscm@7%O2 5.27E-02 5.22E-02 4.51E-02 0.050

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 313.2 249.6 111.2 224.667

Elb/hr 8.98E+01 7.14E+01 3.17E+01 64.300

lb/mmBtuO2 7.08E-02 5.88E-02 2.72E-02 0.052

mg/dscm 6.56E+01 4.86E+01 2.29E+01 45.700

mg/dscm@7%O2 8.21E+01 6.82E+01 3.15E+01 60.600

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.06049 0.04958 0.02998 0.047

Elb/hr 1.73E-02 1.42E-02 8.54E-03 0.013

lb/mmBtuO2 1.37E-05 1.17E-05 7.33E-06 0.000

mg/dscm 1.27E-02 9.65E-03 6.17E-03 0.010

mg/dscm@7%O2 1.59E-02 1.35E-02 8.49E-03 0.013

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.4357 0.4518 0.2871 0.392

Elb/hr 1.25E-01 1.29E-01 8.18E-02 0.112

lb/mmBtuO2 9.86E-05 1.07E-04 7.02E-05 0.000

mg/dscm 9.13E-02 8.79E-02 5.91E-02 0.079

mg/dscm@7%O2 1.14E-01 1.23E-01 8.13E-02 0.106

Tuesday, February 22, 2011 Page 20 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 3.1722 2.9712975 2.5953 2.913

Elb/hr 9.09E-01 8.50E-01 7.40E-01 0.833

lb/mmBtuO2 7.18E-04 7.00E-04 6.35E-04 0.001

mg/dscm 6.64E-01 5.78E-01 5.35E-01 0.592

mg/dscm@7%O2 8.31E-01 8.12E-01 7.36E-01 0.793

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0108 0.0098 0.0056 0.009

Elb/hr 3.09E-03 2.80E-03 1.60E-03 0.002

lb/mmBtuO2 2.44E-06 2.31E-06 1.37E-06 0.000

mg/dscm 2.26E-03 1.91E-03 1.15E-03 0.002

mg/dscm@7%O2 2.83E-03 2.68E-03 1.58E-03 0.002

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 1-1 1-2 1-3

Elb/hr 3.39E+02 3.48E+02 3.51E+02 346.000

lb/mmBtuO2 2.74E-01 2.80E-01 2.84E-01 0.279

mg/dscm 2.33E+02 2.36E+02 2.34E+02 234.333

mg/dscm@7%O2 3.18E+02 3.25E+02 3.29E+02 324.000

ppm 8.76E+01 8.85E+01 8.79E+01 88.000

ppm@7%O2 1.19E+02 1.22E+02 1.23E+02 121.333

Location: Stack Exit - Method 6C 3

Compound: Sulfur Dioxide

Average

Run 3-1 3-2 3-3

Elb/hr 1.08E+02 1.08E+02 1.05E+02 107.000

lb/mmBtuO2 2.53E-01 2.59E-01 2.60E-01 0.257

mg/dscm 1.49E+02 1.51E+02 1.51E+02 150.333

mg/dscm@7%O2 2.93E+02 3.01E+02 3.01E+02 298.333

ppm 5.59E+01 5.66E+01 5.68E+01 56.433

ppm@7%O2 1.10E+02 1.13E+02 1.13E+02 112.000

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 3-1 3-2 3-3

Elb/hr 8.07E+01 7.84E+01 7.48E+01 77.967

lb/mmBtuO2 1.88E-01 1.87E-01 1.85E-01 0.187

mg/dscm 1.11E+02 1.09E+02 1.08E+02 109.333

mg/dscm@7%O2 2.19E+02 2.17E+02 2.15E+02 217.000

ppm 5.80E+01 5.70E+01 5.62E+01 57.067

ppm@7%O2 1.14E+02 1.13E+02 1.12E+02 113.000

Location: Stack Exit - OTM - 27/28

Tuesday, February 22, 2011 Page 21 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Process Run Data

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 76.8 136.4 76.7 96.633

Elb/hr 3.14E+01 5.63E+01 3.12E+01 39.633

gr/dscf 9.67E-03 1.65E-02 9.60E-03 0.012

lb/mmBtuO2 2.39E-02 4.57E-02 2.61E-02 0.032

mg/dscm 2.21E+01 3.77E+01 2.20E+01 27.267

ppm #Num!

Tuesday, February 22, 2011 Page 22 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 

Run 1 M0010 

Start 7/8/2010 

16:24 End 

7/8/2010 18:47

0

10 Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 

Run 1 M0011 

7/8/2010 16:24 

7/8/2010 18:45

0

11 Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 

Runs 1-4 M0031 

7/8/2010 16:24 

7/8/2010 18:25

0

12 Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 

Run 1 M6C (SO2) 

7/8/2010 16:24 

7/8/2010 18:47

0

13 Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 

Run 1 M10 (CO) 

7/8/2010 16:24 

7/8/2010 18:47

0

14 Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 

Run 1 M25A 

(TOC as propane) 

7/8/2010 16:24 

7/8/2010 18:47

0

15 Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 

Run 2 M0010 

7/8/2010 19:45 

7/8/2010 22:01

0

16 Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 

Run 2 M0011 

7/8/2010 19:48 

7/8/2010 21:57

0

17 Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 

Runs 5-8 M0031 

7/8/2010 19:45 

7/8/2010 21:51

0

18 Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 

Run 2 M6C (SO2) 

7/8/2010 19:45 

7/8/2010 22:01

0

19 Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 

Run 2 M10 (CO) 

7/8/2010 19:45 

7/8/2010 22:01

0

Tuesday, February 22, 2011 Page 23 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

20 Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 

Run 2 M25A 

(TOC as propane) 

7/8/2010 19:45 

7/8/2010 22:01

0

21 Fuel Oil Firing Rate 7332 gal/hr SEW3 Group 1 

Run 3 M0010 

7/9/2010 9:06 

7/9/2010 11:15

0

22 Fuel Oil Firing Rate 7332 gal/hr SEW3 Group 1 

Run 3 M0011 

7/9/2010 9:06 

7/9/2010 11:14

0

23 Fuel Oil Firing Rate 7227 gal/hr SEW3 Group 1 

Runs 9-12 M0031 

7/9/2010 9:12 

7/9/2010 11:46

0

24 Fuel Oil Firing Rate 7330 gal/hr SEW3 Group 1 

Run 3 M6C (SO2) 

7/9/2010 9:15 

7/9/2010 11:15

0

25 Fuel Oil Firing Rate 7330 gal/hr SEW3 Group 1 

Run 3 M10 (CO) 

7/9/2010 9:15 

7/9/2010 11:15

0

26 Fuel Oil Firing Rate 7330 gal/hr SEW3 Group 1 

Run 3 M25A 

(TOC as propane) 

7/9/2010 9:15 

7/9/2010 11:15

0

27 Fuel Oil Firing Rate 7182 gal/hr SEW3 Group 1 

Run 1 M18 (CH4) 

7/8/2010 18:50 

7/8/2010 18:54

0

28 Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 

Run 2 M18 (CH4) 

7/8/2010 19:01 

7/8/2010 19:04

0

29 Fuel Oil Firing Rate 7185 gal/hr SEW3 Group 1 

Run 3 M18 (CH4) 

7/8/2010 19:09 

7/8/2010 19:13

0

30 Fuel Oil Firing Rate 2666 gal/hr SEW3 Group 2 

Run 1 M23 

7/7/2010 21:10 

7/8/2010 7:05

0

31 Fuel Oil Firing Rate 4584 gal/hr SEW3 Group 2 

Run 2 M23 

7/8/2010 23:10 

7/9/2010 7:28

0

Tuesday, February 22, 2011 Page 24 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

32 Fuel Oil Firing Rate 2543 gal/hr SEW3 Group 2 

Run 3 M23 

7/9/2010 12:58 

7/9/2010 21:06

0

33 Fuel Oil Firing Rate 2538 gal/hr SEW3 Group 3 

Run 1 M26A 

7/9/2010 12:58 

7/9/2010 14:07

0

34 Fuel Oil Firing Rate 2539 gal/hr SEW3 Group 3 

Run 1 M6C (SO2) 

7/9/2010 12:59 

7/9/2010 14:09

0

35 Fuel Oil Firing Rate 2539 gal/hr SEW3 Group 3 

Run 1 M7E (NOx) 

7/9/2010 12:59 

7/9/2010 14:09

0

36 Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 

Run 2 M26A 

7/9/2010 14:40 

7/9/2010 15:51

0

37 Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 

Run 2 M6C (SO2) 

7/9/2010 14:42 

7/9/2010 15:42

0

38 Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 

Run 2 M7E (NOx) 

7/9/2010 14:42 

7/9/2010 15:42

0

39 Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 

Run 3 M26A 

7/9/2010 16:10 

7/9/2010 17:17

0

4 Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 

Run 3 M6C (SO2) 

7/9/2010 16:12 

7/9/2010 17:11

0

40 Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 

Run 3 M7E (NOx) 

7/9/2010 16:12 

7/9/2010 17:11

0

41 Fuel Oil Firing Rate 7702 gal/hr SEW3 Group 4 

Run 1 M29 

7/6/2010 15:58 

7/6/2010 21:57

0

42 Fuel Oil Firing Rate 7701 gal/hr SEW3 Group 4 

Run 1 

OTM027/028 

7/6/2010 16:00 

7/6/2010 22:05

0

Tuesday, February 22, 2011 Page 25 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

43 Fuel Oil Firing Rate 7717 gal/hr SEW3 Group 4 

Run 1 M30B 

7/6/2010 14:22 

7/6/2010 20:22

0

44 Fuel Oil Firing Rate 7220 gal/hr SEW3 Group 4 

Run 2 M29 

7/7/2010 13:00 

7/7/2010 18:33

0

5 Fuel Oil Firing Rate 7220 gal/hr SEW3 Group 4 

Run 2 

OTM027/028 

7/7/2010 13:00 

7/7/2010 19:08

0

6 Fuel Oil Firing Rate 7220 gal/hr SEW3 Group 4 

Run 2 M30B 

7/7/2010 13:04 

7/7/2010 19:04

0

7 Fuel Oil Firing Rate 7180 gal/hr SEW3 Group 4 

Run 3 M29 

7/8/2010 8:30 

7/8/2010 14:07

0

8 Fuel Oil Firing Rate 7180 gal/hr SEW3 Group 4 

Run 3 

OTM027/028 

7/8/2010 8:30 

7/8/2010 14:17

0

9 Fuel Oil Firing Rate 7180 gal/hr SEW3 Group 4 

Run 3 M30B 

7/8/2010 8:31 

7/8/2010 14:31

0

1 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 1 M0010 

Start 7/8/2010 

16:24 End 

7/8/2010 18:47

0

10 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 1 M0011 

7/8/2010 16:24 

7/8/2010 18:45

0

11 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Runs 1-4 M0031 

7/8/2010 16:24 

7/8/2010 18:25

0

12 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 1 M6C (SO2) 

7/8/2010 16:24 

7/8/2010 18:47

0

13 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 1 M10 (CO) 

7/8/2010 16:24 

7/8/2010 18:47

0

Tuesday, February 22, 2011 Page 26 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

14 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 1 M25A 

(TOC as propane) 

7/8/2010 16:24 

7/8/2010 18:47

0

15 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 2 M0010 

7/8/2010 19:45 

7/8/2010 22:01

0

16 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 2 M0011 

7/8/2010 19:48 

7/8/2010 21:57

0

17 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Runs 5-8 M0031 

7/8/2010 19:45 

7/8/2010 21:51

0

18 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 2 M6C (SO2) 

7/8/2010 19:45 

7/8/2010 22:01

0

19 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 2 M10 (CO) 

7/8/2010 19:45 

7/8/2010 22:01

0

20 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 2 M25A 

(TOC as propane) 

7/8/2010 19:45 

7/8/2010 22:01

0

21 Unit Gross Electrical Output 104 Mwe SEW3 Group 1 

Run 3 M0010 

7/9/2010 9:06 

7/9/2010 11:15

0

22 Unit Gross Electrical Output 104 Mwe SEW3 Group 1 

Run 3 M0011 

7/9/2010 9:06 

7/9/2010 11:14

0

23 Unit Gross Electrical Output 102 Mwe SEW3 Group 1 

Runs 9-12 M0031 

7/9/2010 9:12 

7/9/2010 11:46

0

24 Unit Gross Electrical Output 104 Mwe SEW3 Group 1 

Run 3 M6C (SO2) 

7/9/2010 9:15 

7/9/2010 11:15

0

25 Unit Gross Electrical Output 104 Mwe SEW3 Group 1 

Run 3 M10 (CO) 

7/9/2010 9:15 

7/9/2010 11:15

0

Tuesday, February 22, 2011 Page 27 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

26 Unit Gross Electrical Output 104 Mwe SEW3 Group 1 

Run 3 M25A 

(TOC as propane) 

7/9/2010 9:15 

7/9/2010 11:15

0

27 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 1 M18 (CH4) 

7/8/2010 18:50 

7/8/2010 18:54

0

28 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 2 M18 (CH4) 

7/8/2010 19:01 

7/8/2010 19:04

0

29 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 

Run 3 M18 (CH4) 

7/8/2010 19:09 

7/8/2010 19:13

0

30 Unit Gross Electrical Output 30 Mwe SEW3 Group 2 

Run 1 M23 

7/7/2010 21:10 

7/8/2010 7:05

0

31 Unit Gross Electrical Output 60 Mwe SEW3 Group 2 

Run 2 M23 

7/8/2010 23:10 

7/9/2010 7:28

0

32 Unit Gross Electrical Output 29 Mwe SEW3 Group 2 

Run 3 M23 

7/9/2010 12:58 

7/9/2010 21:06

0

33 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 1 M26A 

7/9/2010 12:58 

7/9/2010 14:07

0

34 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 1 M6C (SO2) 

7/9/2010 12:59 

7/9/2010 14:09

0

35 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 1 M7E (NOx) 

7/9/2010 12:59 

7/9/2010 14:09

0

36 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 2 M26A 

7/9/2010 14:40 

7/9/2010 15:51

0

37 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 2 M6C (SO2) 

7/9/2010 14:42 

7/9/2010 15:42

0

Tuesday, February 22, 2011 Page 28 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

38 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 2 M7E (NOx) 

7/9/2010 14:42 

7/9/2010 15:42

0

39 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 3 M26A 

7/9/2010 16:10 

7/9/2010 17:17

0

4 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 3 M6C (SO2) 

7/9/2010 16:12 

7/9/2010 17:11

0

40 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 

Run 3 M7E (NOx) 

7/9/2010 16:12 

7/9/2010 17:11

0

41 Unit Gross Electrical Output 108 Mwe SEW3 Group 4 

Run 1 M29 

7/6/2010 15:58 

7/6/2010 21:57

0

42 Unit Gross Electrical Output 108 Mwe SEW3 Group 4 

Run 1 

OTM027/028 

7/6/2010 16:00 

7/6/2010 22:05

0

43 Unit Gross Electrical Output 108 Mwe SEW3 Group 4 

Run 1 M30B 

7/6/2010 14:22 

7/6/2010 20:22

0

44 Unit Gross Electrical Output 102 Mwe SEW3 Group 4 

Run 2 M29 

7/7/2010 13:00 

7/7/2010 18:33

0

5 Unit Gross Electrical Output 102 Mwe SEW3 Group 4 

Run 2 

OTM027/028 

7/7/2010 13:00 

7/7/2010 19:08

0

6 Unit Gross Electrical Output 102 Mwe SEW3 Group 4 

Run 2 M30B 

7/7/2010 13:04 

7/7/2010 19:04

0

7 Unit Gross Electrical Output 100 Mwe SEW3 Group 4 

Run 3 M29 

7/8/2010 8:30 

7/8/2010 14:07

0

8 Unit Gross Electrical Output 100 Mwe SEW3 Group 4 

Run 3 

OTM027/028 

7/8/2010 8:30 

7/8/2010 14:17

0

Tuesday, February 22, 2011 Page 29 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

9 Unit Gross Electrical Output 100 Mwe SEW3 Group 4 

Run 3 M30B 

7/8/2010 8:31 

7/8/2010 14:31

0

1 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 1 M0010 

Start 7/8/2010 

16:24 End 

7/8/2010 18:47

0

10 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 1 M0011 

7/8/2010 16:24 

7/8/2010 18:45

0

11 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Runs 1-4 M0031 

7/8/2010 16:24 

7/8/2010 18:25

0

12 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 1 M6C (SO2) 

7/8/2010 16:24 

7/8/2010 18:47

0

13 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 1 M10 (CO) 

7/8/2010 16:24 

7/8/2010 18:47

0

14 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 1 M25A 

(TOC as propane) 

7/8/2010 16:24 

7/8/2010 18:47

0

15 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 2 M0010 

7/8/2010 19:45 

7/8/2010 22:01

0

16 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 2 M0011 

7/8/2010 19:48 

7/8/2010 21:57

0

17 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Runs 5-8 M0031 

7/8/2010 19:45 

7/8/2010 21:51

0

18 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 2 M6C (SO2) 

7/8/2010 19:45 

7/8/2010 22:01

0

19 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 2 M10 (CO) 

7/8/2010 19:45 

7/8/2010 22:01

0

Tuesday, February 22, 2011 Page 30 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

20 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 2 M25A 

(TOC as propane) 

7/8/2010 19:45 

7/8/2010 22:01

0

21 Unit Net Electric Generation 97 MWh SEW3 Group 1 

Run 3 M0010 

7/9/2010 9:06 

7/9/2010 11:15

0

22 Unit Net Electric Generation 97 MWh SEW3 Group 1 

Run 3 M0011 

7/9/2010 9:06 

7/9/2010 11:14

0

23 Unit Net Electric Generation 96 MWh SEW3 Group 1 

Runs 9-12 M0031 

7/9/2010 9:12 

7/9/2010 11:46

0

24 Unit Net Electric Generation 97 MWh SEW3 Group 1 

Run 3 M6C (SO2) 

7/9/2010 9:15 

7/9/2010 11:15

0

25 Unit Net Electric Generation 97 MWh SEW3 Group 1 

Run 3 M10 (CO) 

7/9/2010 9:15 

7/9/2010 11:15

0

26 Unit Net Electric Generation 97 MWh SEW3 Group 1 

Run 3 M25A 

(TOC as propane) 

7/9/2010 9:15 

7/9/2010 11:15

0

27 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 1 M18 (CH4) 

7/8/2010 18:50 

7/8/2010 18:54

0

28 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 2 M18 (CH4) 

7/8/2010 19:01 

7/8/2010 19:04

0

29 Unit Net Electric Generation 94 MWh SEW3 Group 1 

Run 3 M18 (CH4) 

7/8/2010 19:09 

7/8/2010 19:13

0

30 Unit Net Electric Generation 28 MWh SEW3 Group 2 

Run 1 M23 

7/7/2010 21:10 

7/8/2010 7:05

0

31 Unit Net Electric Generation 56 MWh SEW3 Group 2 

Run 2 M23 

7/8/2010 23:10 

7/9/2010 7:28

0

Tuesday, February 22, 2011 Page 31 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

32 Unit Net Electric Generation 27 MWh SEW3 Group 2 

Run 3 M23 

7/9/2010 12:58 

7/9/2010 21:06

0

33 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 1 M26A 

7/9/2010 12:58 

7/9/2010 14:07

0

34 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 1 M6C (SO2) 

7/9/2010 12:59 

7/9/2010 14:09

0

35 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 1 M7E (NOx) 

7/9/2010 12:59 

7/9/2010 14:09

0

36 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 2 M26A 

7/9/2010 14:40 

7/9/2010 15:51

0

37 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 2 M6C (SO2) 

7/9/2010 14:42 

7/9/2010 15:42

0

38 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 2 M7E (NOx) 

7/9/2010 14:42 

7/9/2010 15:42

0

39 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 3 M26A 

7/9/2010 16:10 

7/9/2010 17:17

0

4 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 3 M6C (SO2) 

7/9/2010 16:12 

7/9/2010 17:11

0

40 Unit Net Electric Generation 27 MWh SEW3 Group 3 

Run 3 M7E (NOx) 

7/9/2010 16:12 

7/9/2010 17:11

0

41 Unit Net Electric Generation 101 MWh SEW3 Group 4 

Run 1 M29 

7/6/2010 15:58 

7/6/2010 21:57

0

42 Unit Net Electric Generation 101 MWh SEW3 Group 4 

Run 1 

OTM027/028 

7/6/2010 16:00 

7/6/2010 22:05

0

Tuesday, February 22, 2011 Page 32 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

APCD Run Data

Process Lab Run Data

43 Unit Net Electric Generation 102 MWh SEW3 Group 4 

Run 1 M30B 

7/6/2010 14:22 

7/6/2010 20:22

0

44 Unit Net Electric Generation 95 MWh SEW3 Group 4 

Run 2 M29 

7/7/2010 13:00 

7/7/2010 18:33

0

5 Unit Net Electric Generation 95 MWh SEW3 Group 4 

Run 2 

OTM027/028 

7/7/2010 13:00 

7/7/2010 19:08

0

6 Unit Net Electric Generation 95 MWh SEW3 Group 4 

Run 2 M30B 

7/7/2010 13:04 

7/7/2010 19:04

0

7 Unit Net Electric Generation 94 MWh SEW3 Group 4 

Run 3 M29 

7/8/2010 8:30 

7/8/2010 14:07

0

8 Unit Net Electric Generation 94 MWh SEW3 Group 4 

Run 3 

OTM027/028 

7/8/2010 8:30 

7/8/2010 14:17

0

9 Unit Net Electric Generation 94 MWh SEW3 Group 4 

Run 3 M30B 

7/8/2010 8:31 

7/8/2010 14:31

0

1 Heat Input Million Btus/million BTU using O2 0 0

Run Name Value UOM Comments

Target

Value

1 None 0 0

1 0 0

1 0 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 0 Btu/lb

1 Fuel Moisture 0 %

1 Fuel Mercury Content 0 ppm

1 Fuel Cadmium Content 0 ppm

1 Ultimate/Proximate Analysis 0

Tuesday, February 22, 2011 Page 33 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

1 Fuel Nickel Content 0 ppm

1 Fuel Arsenic Content 0 ppm

1 Fuel Chromium Content 0 ppm

1 Fuel Beryllium Content 0 ppm

1 Fuel Lead Content 0 ppm

1 Fuel Manganese Content 0 ppm

1 Fuel Chlorine Content 0 ppm

1 Fuel Fluorine Content 0 ppm

Tuesday, February 22, 2011 Page 34 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 0011

Average

Run Number 1 2 3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:48:00 PM 9:06:00 AM

Run Finish Time 6:45:00 PM 9:57:00 PM 11:14:00 AM

Net Traversing Points 24 24 24

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.217 0.217 0.219 0.218

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9906 0.9906 0.9906 0.991

Barometric Pressure, inches of Mercury 29.91 29.915 29.89 29.905

Average Orifice Meter Differential, inches H2O 1.40 1.46 1.47 1.443

Dry Gas Meter Volume Sampled, cubic feet 78.180 78.792 81.281 79.418

Average Dry Gas Meter Temperature, °F 104.81 99.10 98.77 100.893

Dry Gas Meter Volume Sampled, dscf 72.623 73.962 76.282 74.289

Total Moisture Liquid collected, g 139.8 150.4 145.6 145.267

Volume of Water Vapor, standard cubic feet 6.58 7.08 6.85 6.837

Moisture Content of Stack Gas, % 8.31 8.74 8.24 8.430

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9169 0.9126 0.9176 0.916

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Carbon Monoxide & Nitrogen, % 81.7 81.6 81.6 81.633

Fuel Factor 1.34 1.33 1.34

Dry Molecular Weight, lb/lb-Mole 29.64 29.65 29.62 29.637

Wet Molecular weight, lb/lb-Mole 28.67 28.63 28.66 28.653

Flue Gas Static Pressure, inches of H2O 0.2 0.2 0.2 0.200

Absolute Flue Gas Pressure, inches of Mercury 29.92 29.93 29.90 29.917

Average Stack Gas Temperature, °F 258.92 256.92 260.50 258.780

Average Velocity Head, inches of H2O 0.8376328350

82385

0.891715552

496708

0.888728642

560459

0.873

Average Stack Gas Velocity, feet/second 60.17 62.03 62.08 61.427

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 388,522.3 399,899.8 400,014.1 396,145.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 576,953.3 594,788.3 595,267.7 589,003.100

Percent Isokinetic of Sampling Rate, % 96.9 95.9 97.1 96.633

Percent Excess Air, % 98.4 100.5 104.3 101.067

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 35 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 10

Average

Run Number 1-1 1-2 1-3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:45:00 PM 9:15:00 AM

Run Finish Time 6:47:00 PM 10:01:00 PM 11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Fuel Factor 1.34 1.33 1.34

Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5 394,229.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.85 9.02 8.07 8.647

Analyzer Make Thermo 

Scientific

Thermo 

Scientific

Thermo 

Scientific

Analyzer Model 48i 48i 48i

Analyzer Serial Number CMO8460052 CMO846005

2

CMO846005

2

Operating Range 99.5 99.5 99.5 99.500

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 110 110 113 111.000

Calibration Pre Zero Cylinder ID Nitrogen-CO Nitrogen-CO Nitrogen-CO

Calibration Pre Zero Cylinder Instrument Response 0.341 0.048 0.341 0.243

Calibration Pre Zero Cylinder Bias 0.34 0.05 0.32 0.237

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM00000-

CO-Mid

ALM00000-

CO-Mid

ALM00000-

CO-Mid

Calibration Pre High Cylinder Instrument Response 48.852 49.047 49.951 49.283

Calibration Pre High Cylinder Bias -1.35 -1.15 -0.71 -1.070

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-CO Nitrogen-CO Nitrogen-CO

Calibration Post Zero Cylinder Instrument Response 0.048 0.146 0.097 0.097

Calibration Post Zero Cylinder Bias 0.05 0.15 0.07 0.090

Calibration Post Zero Cylinder Drift 0.29 0.1 0.25 0.213

Calibration Post High Cylinder ID ALM00000-

CO-Mid

ALM00000-

CO-Mid

ALM00000-

CO-Mid

Calibration Post High Cylinder Instrument Response 49.047 49.536 49.926 49.503

Calibration Post High Cylinder Bias -1.15 -0.66 -0.74 -0.850

Calibration Post High Cylinder Drift 0.2 0.49 0.03 0.240

Cavg 0.9 0.8 -0.1 0.533

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.725 0.7159 0 0.480

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 36 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 7/7/2010 7/8/2010 7/9/2010

Run Start Time 7:04:00 AM 7:28:00 AM 12:58:00 PM

Run Finish Time 9:10:00 PM 11:10:00 PM 9:06:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 576 480 480

Nozzle Diameter, inches 0.288 0.288 0.316 0.297

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988

Barometric Pressure, inches of Mercury 29.9 29.915 29.815 29.877

Average Orifice Meter Differential, inches H2O 1.14 2.51 1.52 1.723

Dry Gas Meter Volume Sampled, cubic feet 354.728 419.684 334.505 369.639

Average Dry Gas Meter Temperature, °F 92.33 93.58 91.71 92.540

Dry Gas Meter Volume Sampled, dscf 335.816 397.942 316.423 350.060

Total Moisture Liquid collected, g 516.5 643.8 482.4 547.567

Volume of Water Vapor, standard cubic feet 24.31 30.30 22.71 25.773

Moisture Content of Stack Gas, % 6.75 7.08 6.70 6.843

Moisture Saturation at Stack Gas Temperature, % 97.13 100.00 93.65 96.927

Dry Mole Fraction 0.9325 0.9292 0.933 0.932

Carbon Dioxide, % 5.3 6.4 5.1 5.600

Oxygen, % 13.9 12.5 13.8 13.400

Carbon Monoxide & Nitrogen, % 80.8 81.1 81.1 81.000

Fuel Factor 1.32 1.31 1.39

Dry Molecular Weight, lb/lb-Mole 29.40 29.52 29.37 29.430

Wet Molecular weight, lb/lb-Mole 28.63 28.70 28.61 28.647

Flue Gas Static Pressure, inches of H2O 0.26 0.28 -0.09 0.150

Absolute Flue Gas Pressure, inches of Mercury 29.92 29.94 29.81 29.890

Average Stack Gas Temperature, °F 210.54 233.54 208.54 217.540

Average Velocity Head, inches of H2O 0.2166688140

80506

0.509863524

527934

0.196367798

633064

0.308

Average Stack Gas Velocity, feet/second 29.57 46.07 28.17 34.603

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 208,194.9 312,709.2 198,306.1 239,736.733

Actual Wet Volumetric Flue Gas Flow Rate, acfm 283,538.5 441,752.3 270,114.2 331,801.667

Percent Isokinetic of Sampling Rate, % 98.9 93.7 97.5 96.700

Percent Excess Air, % 187.0 140.3 181.3 169.533

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 37 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 25A

Average

Run Number 1-1 1-2 1-3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:45:00 PM 9:15:00 AM

Run Finish Time 6:47:00 PM 10:01:00 PM 11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Fuel Factor 1.34 1.33 1.34

Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5 394,229.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.31 8.94 8.24 8.497

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 51C 51C 51C

Analyzer Serial Number 0327202203 0327202203 0327202203 327,202,203

.000

Operating Range 10 10 10 10.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 111 111 220 147.333

Calibration Pre Zero Cylinder ID Nitrogen-THC NitrogenTHCNitrogenTHC

Calibration Pre Zero Cylinder Instrument Response -0.034 0.002 0.012 -0.007

Calibration Pre Zero Cylinder Bias -0.34 0.02 0.08 -0.080

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID BBB00000-

THC-Low

BBB00000-

THC-Low

BBB00000-

THC-Low

Calibration Pre High Cylinder Instrument Response 2.98 2.961 3.051 2.997

Calibration Pre High Cylinder Bias -1.2 -1.39 -0.59 -1.060

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-THC NitrogenTHCNitrogenTHC

Calibration Post Zero Cylinder Instrument Response 0.002 -0.222 0.004 -0.072

Calibration Post Zero Cylinder Bias 0.02 -2.22 0 -0.733

Calibration Post Zero Cylinder Drift 0.36 2.24 0.08 0.893

Calibration Post High Cylinder ID BBB00000-

THC-Low

BBB00000-

THC-Low

BBB00000-

THC-Low

Calibration Post High Cylinder Instrument Response 2.961 2.79 3.032 2.928

Calibration Post High Cylinder Bias -1.39 -3.1 -0.78 -1.757

Calibration Post High Cylinder Drift 0.19 1.71 0.19 0.697

Cavg 0.4 0.2 0.1 0.233

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.4179 0.3115 0.091 0.273

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 38 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 7/9/2010 7/9/2010 7/9/2010

Run Start Time 12:58:00 PM 2:40:00 PM 4:10:00 PM

Run Finish Time 2:07:00 PM 3:51:00 PM 5:17:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.318 0.318 0.318 0.318

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9906 0.9906 0.9906 0.991

Barometric Pressure, inches of Mercury 29.84 29.8 29.765 29.802

Average Orifice Meter Differential, inches H2O 1.68 1.55 1.56 1.597

Dry Gas Meter Volume Sampled, cubic feet 42.643 41.841 41.816 42.100

Average Dry Gas Meter Temperature, °F 99.60 101.90 102.98 101.493

Dry Gas Meter Volume Sampled, dscf 39.915 38.939 38.797 39.217

Total Moisture Liquid collected, g 92.2 88.6 84.6 88.467

Volume of Water Vapor, standard cubic feet 4.34 4.17 3.98 4.163

Moisture Content of Stack Gas, % 9.81 9.67 9.30 9.593

Moisture Saturation at Stack Gas Temperature, % 92.57 88.94 88.27 89.927

Dry Mole Fraction 0.9019 0.9033 0.907 0.904

Carbon Dioxide, % 5.162 5.198 5.185 5.182

Oxygen, % 13.841 13.918 13.929 13.896

Carbon Monoxide & Nitrogen, % 80.997 80.884 80.886 80.922

Fuel Factor 1.37 1.34 1.34

Dry Molecular Weight, lb/lb-Mole 29.38 29.39 29.39 29.387

Wet Molecular weight, lb/lb-Mole 28.26 28.29 28.33 28.293

Flue Gas Static Pressure, inches of H2O -0.09 -0.09 -0.09 -0.090

Absolute Flue Gas Pressure, inches of Mercury 29.83 29.79 29.76 29.793

Average Stack Gas Temperature, °F 208.00 205.96 205.54 206.500

Average Velocity Head, inches of H2O 0.1991035484

11154

0.180662510

719094

0.180474966

099066

0.187

Average Stack Gas Velocity, feet/second 28.52 27.13 27.11 27.587

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 194,364.8 185,497.1 186,049.5 188,637.133

Actual Wet Volumetric Flue Gas Flow Rate, acfm 273,470.3 260,142.0 259,950.2 264,520.833

Percent Isokinetic of Sampling Rate, % 99.2 101.4 100.7 100.433

Percent Excess Air, % 183.5 187.2 187.6 186.100

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 39 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 7/6/2010 7/7/2010 7/8/2010

Run Start Time 3:58:00 PM 1:00:00 PM 8:30:00 AM

Run Finish Time 9:27:00 PM 6:33:00 PM 2:07:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 300 300 300

Nozzle Diameter, inches 0.213 0.215 0.214 0.214

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988

Barometric Pressure, inches of Mercury 29.855 29.89 29.935 29.893

Average Orifice Meter Differential, inches H2O 1.10 1.25 1.09 1.147

Dry Gas Meter Volume Sampled, cubic feet 185.800 196.161 183.044 188.335

Average Dry Gas Meter Temperature, °F 115.17 105.25 98.71 106.377

Dry Gas Meter Volume Sampled, dscf 168.639 181.447 171.485 173.857

Total Moisture Liquid collected, g 327.9 330.5 322.3 326.900

Volume of Water Vapor, standard cubic feet 15.43 15.56 15.17 15.387

Moisture Content of Stack Gas, % 8.38 7.90 8.13 8.137

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9162 0.921 0.9187 0.919

Carbon Dioxide, % 8.5 7.3 7.5 7.767

Oxygen, % 9.8 11 10.8 10.533

Carbon Monoxide & Nitrogen, % 81.7 81.7 81.7 81.700

Fuel Factor 1.31 1.36 1.35

Dry Molecular Weight, lb/lb-Mole 29.75 29.61 29.63 29.663

Wet Molecular weight, lb/lb-Mole 28.77 28.69 28.68 28.713

Flue Gas Static Pressure, inches of H2O -0.31 0.2 -0.2 -0.103

Absolute Flue Gas Pressure, inches of Mercury 29.83 29.90 29.92 29.883

Average Stack Gas Temperature, °F 294.96 271.29 259.42 275.223

Average Velocity Head, inches of H2O 0.7840257178

18982

0.861641761

642179

0.755544851

668207

0.800

Average Stack Gas Velocity, feet/second 59.64 61.55 57.15 59.447

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 365,334.1 392,195.1 369,489.4 375,672.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 571,871.3 590,185.7 547,995.3 570,017.433

Percent Isokinetic of Sampling Rate, % 99.4 97.8 99.0 98.733

Percent Excess Air, % 83.3 104.1 100.3 95.900

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 40 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 6C

Average

Run Number 1-1 1-2 1-3

Test Date 7/8/2010 7/8/2010 7/9/2010

Run Start Time 4:24:00 PM 7:45:00 PM 9:15:00 AM

Run Finish Time 6:47:00 PM 10:01:00 PM 11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533

Oxygen, % 10.7 10.8 11 10.833

Fuel Factor 1.34 1.33 1.34

Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5 394,229.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.85 9.02 8.07 8.647

Analyzer Make Ametek Ametek Ametek

Analyzer Model 921CE 921CE 921CE

Analyzer Serial Number AE-921-6434 AE-921-

6434

AE-921-6434

Operating Range 201 201 201 201.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 3 3 111 39.000

Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Pre Zero Cylinder Instrument Response 1.77 1.279 1.475 1.508

Calibration Pre Zero Cylinder Bias 1.12 0.88 1.08 1.027

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM045659-

SO2-Mid

ALM045659

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Pre High Cylinder Instrument Response 99.175 96.224 95.732 97.044

Calibration Pre High Cylinder Bias 0 -1.47 -3.38 -1.617

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Post Zero Cylinder Instrument Response 1.279 2.066 3.443 2.263

Calibration Post Zero Cylinder Bias 0.88 1.27 2.06 1.403

Calibration Post Zero Cylinder Drift 0.24 0.39 0.98 0.537

Calibration Post High Cylinder ID ALM045659-

SO2-Mid

ALM045659

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Post High Cylinder Instrument Response 96.224 96.42 95.732 96.125

Calibration Post High Cylinder Bias -1.47 -1.37 -3.38 -2.073

Calibration Post High Cylinder Drift 1.47 9.999999999

99999E-02

0 0.523

Cavg 86.6 86.3 85.3 86.067

Cavg Units ppmvd ppmvd ppmvd

Cgas 87.5745 88.5173 87.9275 88.006

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 41 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 6C 3

Average

Run Number 3-1 3-2 3-3

Test Date 7/9/2010 7/9/2010 7/9/2010

Run Start Time 12:59:00 PM 2:42:00 PM 4:12:00 PM

Run Finish Time 2:09:00 PM 3:42:00 PM 5:11:00 PM

Carbon Dioxide, % 5.162 5.198 5.185 5.182

Oxygen, % 13.841 13.918 13.929 13.896

Fuel Factor 1.37 1.34 1.34

Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775 190,654.633

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.5 5.5 5.5 5.500

Analyzer Make Ametek Ametek Ametek

Analyzer Model 921CE 921CE 921CE

Analyzer Serial Number AE-921-6434 AE-921-

6434

AE-921-6434

Operating Range 201 201 201 201.000

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 312 312 312 312.000

Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Pre Zero Cylinder Instrument Response 3.443 2.853 2.853 3.050

Calibration Pre Zero Cylinder Bias 2.06 1.76 1.76 1.860

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM045659-

SO2-Mid

ALM045659

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Pre High Cylinder Instrument Response 95.732 96.027 96.716 96.158

Calibration Pre High Cylinder Bias -3.38 -3.23 -2.89 -3.167

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2

Calibration Post Zero Cylinder Instrument Response 2.853 2.853 2.262 2.656

Calibration Post Zero Cylinder Bias 1.76 1.76 1.47 1.663

Calibration Post Zero Cylinder Drift 0.3 0 0.29 0.197

Calibration Post High Cylinder ID ALM045659-

SO2-Mid

ALM045659

-SO2-Mid

ALM045659-

SO2-Mid

Calibration Post High Cylinder Instrument Response 96.027 96.716 97.601 96.781

Calibration Post High Cylinder Bias -3.23 -2.89 -2.45 -2.857

Calibration Post High Cylinder Drift 0.15 0.34 0.44 0.310

Cavg 55.546 56.354 56.831 56.244

Cavg Units ppmvd ppmvd ppmvd

Cgas 55.94 56.6369 56.7972 56.458

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 42 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - Method 7E

Average

Run Number 3-1 3-2 3-3

Test Date 7/9/2010 7/9/2010 7/9/2010

Run Start Time 12:59:00 PM 2:42:00 PM 4:12:00 PM

Run Finish Time 2:09:00 PM 3:42:00 PM 5:11:00 PM

Carbon Dioxide, % 5.162 5.198 5.185 5.182

Oxygen, % 13.841 13.918 13.929 13.896

Fuel Factor 1.37 1.34 1.34

Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775 190,654.633

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 5.5 5.5 5.5 5.500

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 42 CLS 42CLS 42 CLS

Analyzer Serial Number 0328202427 0328202427 0328202427 328,202,427

.000

Operating Range 201 201 201 201.000

Operating Units ppm ppm ppm

No. Readings/Avg. 60 60 60 60.000

Calibration Set 11 11 11 11.000

Calibration Pre Zero Cylinder ID Nitrogen-Nox NitrogenNoxNitrogen-Nox

Calibration Pre Zero Cylinder Instrument Response 0.878 0.488 0.683 0.683

Calibration Pre Zero Cylinder Bias 0.29 0.1 0.19 0.193

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM045659-

NOx-Mid

ALM045659

-NOx-Mid

ALM045659-

NOx-Mid

Calibration Pre High Cylinder Instrument Response 94.531 95.361 96.191 95.361

Calibration Pre High Cylinder Bias -1.11 -0.7 -0.29 -0.700

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen-Nox NitrogenNoxNitrogen-Nox

Calibration Post Zero Cylinder Instrument Response 0.488 0.683 0.732 0.634

Calibration Post Zero Cylinder Bias 0.1 0.19 0.22 0.170

Calibration Post Zero Cylinder Drift 0.19 0.09 0.03 0.103

Calibration Post High Cylinder ID ALM045659-

NOx-Mid

ALM045659

-NOx-Mid

ALM045659-

NOx-Mid

Calibration Post High Cylinder Instrument Response 95.361 96.191 96.142 95.898

Calibration Post High Cylinder Bias -0.7 -0.29 -0.31 -0.433

Calibration Post High Cylinder Drift 0.41 0.41 0.02 0.280

Cavg 55.75 55.329 54.794 55.291

Cavg Units ppmvd ppmvd ppmvd

Cgas 57.9511 57.0493 56.2061 57.069

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Tuesday, February 22, 2011 Page 43 of 44
2411 PSEG Sewaren Unit 3

9/30/2010

Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 7/6/2010 7/7/2010 7/8/2010

Run Start Time 4:00:00 PM 1:00:00 PM 8:30:00 AM

Run Finish Time 10:05:00 PM 7:08:00 PM 2:17:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 338.77 347.94 330.31

Nozzle Diameter, inches 0.17 0.171 0.171 0.171

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9906 0.9906 0.9906 0.991

Barometric Pressure, inches of Mercury 29.855 29.895 29.935 29.895

Average Orifice Meter Differential, inches H2O 0.49 0.49 0.49 0.490

Dry Gas Meter Volume Sampled, cubic feet 134.099 137.887 130.547 134.178

Average Dry Gas Meter Temperature, °F 111.63 105.00 94.88 103.837

Dry Gas Meter Volume Sampled, dscf 122.581 127.693 123.265 124.513

Total Moisture Liquid collected, g 237.4 235.1 241.2 237.900

Volume of Water Vapor, standard cubic feet 11.17 11.07 11.35 11.197

Moisture Content of Stack Gas, % 8.35 7.98 8.43 8.253

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9165 0.9202 0.9157 0.917

Carbon Dioxide, % 8.5 7.3 7.5 7.767

Oxygen, % 9.8 11 10.8 10.533

Carbon Monoxide & Nitrogen, % 81.7 81.7 81.7 81.700

Fuel Factor 1.31 1.36 1.35

Dry Molecular Weight, lb/lb-Mole 29.75 29.61 29.63 29.663

Wet Molecular weight, lb/lb-Mole 28.77 28.68 28.65 28.700

Flue Gas Static Pressure, inches of H2O 0.2 0.2 0.2 0.200

Absolute Flue Gas Pressure, inches of Mercury 29.87 29.91 29.95 29.910

Average Stack Gas Temperature, °F 292.50 267.42 257.25 272.390

Average Velocity Head, inches of H2O 0.8405864811

40868

0.885105045

778335

0.798758400

296064

0.841

Average Stack Gas Velocity, feet/second 61.61 62.21 58.68 60.833

Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812

Dry Volumetric Flow Rate, dry scfm 379,267.3 398,296.6 379,666.7 385,743.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 590,761.0 596,514.3 562,666.1 583,313.800

Percent Isokinetic of Sampling Rate, % 96.7 92.3 98.5 95.833

Percent Excess Air, % 83.3 104.1 100.3 95.900

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 14.263 14.263 14.263

Rectangular Duct Width, inches 151.7 151.7 151.7

Rectangular Duct Length, inches 151.7 151.7 151.7

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Tuesday, February 22, 2011 Page 44 of 44