### Name: Lois A. Knowlson

Title: Senior Environmental Engineer Company: PSEG Fossil Sign Date: 9/30/2010 Name: Anthony Fortunato Title: Senior Test Engineer Company:PSEG Maplewood Testing Services Sign Date: 9/30/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## 2411 PSEG Sewaren Unit 3 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Tuesday, February 22, 2011 Page 1 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Facility Information: 2411 PSEG Sewaren Generating Station
751 Cliff Road

Sewaren NJ07077 Contact:Joseph D. Krejsa Phone:732-750-2001 Fax: Email: joseph.krejsa@pseg.com Testing Company: PSG Maplewood Testing Services 200 Boyden Avenue

Maplewood NJ07040 Contact:Anthony Fortunato Phone:973-761-1005 Fax: Email:anthony.fortunato2@pseg.com

Air Permit Number: 2411-NJDEP PI 18068, BOP 080001 Permitted Source ID/Name: 3 U3 Permitted Maximum Process Rate: 1600 MMBtu/hr Max. Normal Operation Process Rate: 1600 MMBtu/hr Target Process Test Rate N/A

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: External combustion, electric generating unit, tangentially fired, combusting natural gas or #6 fuel oil; no control equipment Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:110000869150 FRS #:110000801614

SCC / Description10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Tangential Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack Exit 14.263 487 1579 4 14.263 4 151.7 151.7

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location % H2O Method 1 - 4 3 180 0 Stack Exit Carbon Monoxide Method 10 3 120 0 Stack Exit Formaldehyde Method 0011 3 120 0 Stack Exit Regulation Description Compound Limit Unit NJAC 7:27-4.2(a) Particulate 160 lb/hr NJAC 7:27-16.8(b)1 Volatile Organic Compounds (total) 50 ppm corrected
NJAC 7:27-16.8(b)2 Carbon Monoxide 100 ppm corrected



### Tuesday, February 22, 2011 Page 2 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 2,3,7,8-TCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 Stack Exit OCDD Method 23 3 480 0 Stack Exit 2,3,7,8-TCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0 Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 Stack Exit OCDF Method 23 3 480 0 Stack Exit Other TCDD Method 23 0 Stack Exit Other PeCDD Method 23 0 Stack Exit Other HxCDD Method 23 0 Stack Exit Other HpCDD Method 23 0 Stack Exit Other TCDF Method 23 0 Stack Exit Other PeCDF Method 23 0 Stack Exit Other HxCDF Method 23 0 Stack Exit Other HpCDF Method 23 0 Stack Exit Total Dioxins Method 23 3 480 0 Stack Exit Total Furans Method 23 3 480 0 Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0 Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 Stack Exit 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 Stack Exit

2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 0 Stack Exit 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 0 Stack Exit 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 Stack Exit
Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Exit
Hydrogen Fluoride Method 26A 3 180 0 Stack Exit Hydrogen Chloride Method 26A 3 180 0 Stack Exit Hydrogen Fluoride Method 26 3 180 0 Stack Exit Hydrogen Chloride Method 26 3 180 0 Stack Exit Filterable PM2.5 OTM - 27/28 3 240 0 Stack Exit Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 240 0 Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Stack Exit Total PM2.5 OTM - 27/28 3 240 0 Stack Exit Total Particulate OTM - 27/28 3 240 0 Stack Exit



### Tuesday, February 22, 2011 Page 3 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
None Organic Condensible

Particulate OTM - 27/28 3 240 0 Stack Exit

Lead Method 29 3 240 0 Stack Exit Manganese Method 29 3 240 0 Stack Exit Nickel Method 29 3 240 0 Stack Exit Selenium Method 29 3 240 0 Stack Exit Filterable Particulate Method 29 3 240 0 Stack Exit Cadmium Method 29 3 240 0 Stack Exit Chromium Method 29 3 240 0 Stack Exit Cobalt Method 29 3 240 0 Stack Exit Arsenic Method 29 3 240 0 Stack Exit Antimony Method 29 3 240 0 Stack Exit Beryllium Method 29 3 240 0 Stack Exit O2 Method 3A O2 3 120 0 Stack Exit Co2 Method 3A CO2 3 120 0 Stack Exit Organic Condensible

Particulate Method 5/OTM-28 3 240 0 Stack Exit
Inorganic (Aqueous)

Condensible Part. Method 5/OTM-28 3 240 0 Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Stack Exit Filterable Particulate Method 5/OTM-28 3 240 0 Stack Exit Sulfur Dioxide Method 6C 3 180 0 Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0 Stack Exit



### Tuesday, February 22, 2011 Page 4 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Sampling / Stack Data Results Summary



### LocationStack Exit - Method 0011 Average Run Number 1 2 3
Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:48:00 PM 9:06:00 AM Run Finish Time 6:45:00 PM9:57:00 PM11:14:00 AM Net Run Time, minutes 120 120 120 Dry Gas Meter Volume Sampled, dscf 72.623 73.962 76.282 74.289 Moisture Content of Stack Gas, % 8.31 8.74 8.24 8.430 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Average Stack Gas Temperature, °F 258.92 256.92 260.50 258.780 Dry Volumetric Flow Rate, dry scfm 388,522.3 399,899.8 400,014.1 396,145.400 Actual Wet Volumetric Flue Gas Flow Rate, acfm 576,953.3 594,788.3 595,267.7589,003.100 Percent Isokinetic of Sampling Rate, % 96.9 95.9 97.1 96.633 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 10 Average Run Number 1-1 1-2 1-3
Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:45:00 PM 9:15:00 AM Run Finish Time 6:47:00 PM 10:01:00 PM11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5394,229.267 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.85 9.02 8.07 8.647 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 5 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 23 Average Run Number 1 2 3
Test Date 7/7/2010 7/8/2010 7/9/2010 Run Start Time 7:04:00 AM 7:28:00 AM12:58:00 PM

Run Finish Time 9:10:00 PM 11:10:00 PM 9:06:00 PM

Net Run Time, minutes 576 480 480 Dry Gas Meter Volume Sampled, dscf 335.816 397.942 316.423 350.060 Moisture Content of Stack Gas, % 6.75 7.08 6.70 6.843 Moisture Saturation at Stack Gas Temperature, % 97.13 100.00 93.65 96.927 Carbon Dioxide, % 5.3 6.4 5.1 5.600 Oxygen, % 13.9 12.5 13.8 13.400 Average Stack Gas Temperature, °F 210.54 233.54 208.54 217.540 Dry Volumetric Flow Rate, dry scfm 208,194.9 312,709.2 198,306.1 239,736.733 Actual Wet Volumetric Flue Gas Flow Rate, acfm 283,538.5 441,752.3 270,114.2331,801.667 Percent Isokinetic of Sampling Rate, % 98.9 93.7 97.5 96.700 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 25A Average Run Number 1-1 1-2 1-3
Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:45:00 PM 9:15:00 AM Run Finish Time 6:47:00 PM 10:01:00 PM11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5394,229.267 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.31 8.94 8.24 8.497 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 6 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 26A Average Run Number 1 2 3
Test Date 7/9/2010 7/9/2010 7/9/2010 Run Start Time 12:58:00 PM2:40:00 PM 4:10:00 PM Run Finish Time 2:07:00 PM3:51:00 PM 5:17:00 PM Net Run Time, minutes 60 60 60 Dry Gas Meter Volume Sampled, dscf 39.915 38.939 38.797 39.217 Moisture Content of Stack Gas, % 9.81 9.67 9.30 9.593 Moisture Saturation at Stack Gas Temperature, % 92.57 88.94 88.27 89.927 Carbon Dioxide, % 5.162 5.198 5.185 5.182 Oxygen, % 13.841 13.918 13.929 13.896 Average Stack Gas Temperature, °F 208.00 205.96 205.54 206.500 Dry Volumetric Flow Rate, dry scfm 194,364.8 185,497.1 186,049.5 188,637.133 Actual Wet Volumetric Flue Gas Flow Rate, acfm 273,470.3 260,142.0 259,950.2264,520.833 Percent Isokinetic of Sampling Rate, % 99.2 101.4 100.7 100.433 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 29 Average Run Number 1 2 3
Test Date 7/6/2010 7/7/2010 7/8/2010 Run Start Time 3:58:00 PM1:00:00 PM 8:30:00 AM Run Finish Time 9:27:00 PM6:33:00 PM 2:07:00 PM Net Run Time, minutes 300 300 300 Dry Gas Meter Volume Sampled, dscf 168.639 181.447 171.485 173.857 Moisture Content of Stack Gas, % 8.38 7.90 8.13 8.137 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 8.5 7.3 7.5 7.767 Oxygen, % 9.8 11 10.8 10.533 Average Stack Gas Temperature, °F 294.96 271.29 259.42 275.223 Dry Volumetric Flow Rate, dry scfm 365,334.1 392,195.1 369,489.4375,672.867 Actual Wet Volumetric Flue Gas Flow Rate, acfm 571,871.3 590,185.7 547,995.3570,017.433 Percent Isokinetic of Sampling Rate, % 99.4 97.8 99.0 98.733 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 7 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 6C Average Run Number 1-1 1-2 1-3
Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:45:00 PM 9:15:00 AM Run Finish Time 6:47:00 PM 10:01:00 PM11:15:00 AM

Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5394,229.267 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 8.85 9.02 8.07 8.647 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - Method 6C 3 Average Run Number 3-1 3-2 3-3
Test Date 7/9/2010 7/9/2010 7/9/2010 Run Start Time 12:59:00 PM2:42:00 PM 4:12:00 PM Run Finish Time 2:09:00 PM3:42:00 PM 5:11:00 PM Carbon Dioxide, % 5.162 5.198 5.185 5.182 Oxygen, % 13.841 13.918 13.929 13.896 Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775 190,654.633 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 5.5 5.5 5.5 5.500 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 8 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 7E Average Run Number 3-1 3-2 3-3
Test Date 7/9/2010 7/9/2010 7/9/2010 Run Start Time 12:59:00 PM2:42:00 PM 4:12:00 PM Run Finish Time 2:09:00 PM3:42:00 PM 5:11:00 PM Carbon Dioxide, % 5.162 5.198 5.185 5.182 Oxygen, % 13.841 13.918 13.929 13.896 Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775 190,654.633 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Moisture, % 5.5 5.5 5.5 5.500 Fuel Type Oil Oil Oil
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### LocationStack Exit - OTM - 27/28 Average Run Number 1 2 3
Test Date 7/6/2010 7/7/2010 7/8/2010 Run Start Time 4:00:00 PM1:00:00 PM 8:30:00 AM
Run Finish Time 10:05:00 PM7:08:00 PM 2:17:00 PM Net Run Time, minutes 338.77 347.94 330.31 Dry Gas Meter Volume Sampled, dscf 122.581 127.693 123.265 124.513 Moisture Content of Stack Gas, % 8.35 7.98 8.43 8.253 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 8.5 7.3 7.5 7.767 Oxygen, % 9.8 11 10.8 10.533 Average Stack Gas Temperature, °F 292.50 267.42 257.25 272.390 Dry Volumetric Flow Rate, dry scfm 379,267.3 398,296.6 379,666.7385,743.533 Actual Wet Volumetric Flue Gas Flow Rate, acfm 590,761.0 596,514.3 562,666.1 583,313.800 Percent Isokinetic of Sampling Rate, % 96.7 92.3 98.5 95.833 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Tuesday, February 22, 2011 Page 9 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Emissions Summary



### Location: Stack Exit - Method 0011 Compound: Formaldehyde Average RunNumber 1 2 3 Mass_mg 0.28 0.24 0.11 0.210 lb/mmBtuO2 1.60E-04 1.36E-04 6.17E-05 0.000



### Location: Stack Exit - Method 10 Compound: Carbon Monoxide Average Run 1-1 1-2 1-3 Elb/hr 1.23E+00 1.23E+00 0.00E+00 0.820 gr/dscf 3.69E-04 3.64E-04 0.00E+00 0.000 lb/mmBtuO2 9.92E-04 9.90E-04 0.00E+00 0.001 mg/dscm 8.44E-01 8.34E-01 0.00E+00 0.559 ppm 7.25E-01 7.16E-01 0.00E+00 0.480 ppm@7%O2 9.88E-01 9.85E-01 0.00E+00 0.658



### Location: Stack Exit - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000019 0.0000000035 0.0000000017 0.000 Elb/hr 1.56E-10 3.64E-10 1.41E-10 0.000 gr/dscf 8.73E-14 1.36E-13 8.29E-14 0.000 lb/mmBtuO2 3.42E-13 4.43E-13 3.20E-13 0.000 mg/dscm 2.00E-10 3.11E-10 1.90E-10 0.000 ng/dscm 2.00E-04 3.11E-04 1.90E-04 0.000 ng/dscm@7%O2 3.97E-04 5.15E-04 3.72E-04 0.000 ppm 1.13E-11 1.76E-11 1.07E-11 0.000 

### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000021 0.0000000029 0.0000000019 0.000 Elb/hr 1.72E-10 3.01E-10 1.58E-10 0.000 gr/dscf 9.65E-14 1.12E-13 9.27E-14 0.000 lb/mmBtuO2 3.78E-13 3.67E-13 3.58E-13 0.000 mg/dscm 2.21E-10 2.57E-10 2.12E-10 0.000 ng/dscm 2.21E-04 2.57E-04 2.12E-04 0.000 ng/dscm@7%O2 4.39E-04 4.25E-04 4.15E-04 0.000 ppm 1.30E-11 1.51E-11 1.25E-11 0.000 

### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000018 0.0000000034 0.0000000018 0.000 Elb/hr 1.48E-10 3.53E-10 1.49E-10 0.000 gr/dscf 8.27E-14 1.32E-13 8.78E-14 0.000 lb/mmBtuO2 3.24E-13 4.31E-13 3.39E-13 0.000



### Tuesday, February 22, 2011 Page 10 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 mg/dscm 1.89E-10 3.02E-10 2.01E-10 0.000 ng/dscm 1.89E-04 3.02E-04 2.01E-04 0.000 ng/dscm@7%O2 3.75E-04 5.00E-04 3.94E-04 0.000 ppm 1.11E-11 1.77E-11 1.18E-11 0.000 

### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000018 0.0000000039 0.0000000017 0.000 Elb/hr 1.48E-10 4.05E-10 1.41E-10 0.000 gr/dscf 8.27E-14 1.51E-13 8.29E-14 0.000 lb/mmBtuO2 3.24E-13 4.94E-13 3.20E-13 0.000 mg/dscm 1.89E-10 3.46E-10 1.90E-10 0.000 ng/dscm 1.89E-04 3.46E-04 1.90E-04 0.000 ng/dscm@7%O2 3.75E-04 5.73E-04 3.72E-04 0.000 ppm 1.16E-11 2.13E-11 1.17E-11 0.000 

### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000015 0.0000000037 0.0000000015 0.000 Elb/hr 1.23E-10 3.85E-10 1.24E-10 0.000 gr/dscf 6.89E-14 1.43E-13 7.32E-14 0.000 lb/mmBtuO2 2.70E-13 4.69E-13 2.83E-13 0.000 mg/dscm 1.58E-10 3.28E-10 1.67E-10 0.000 ng/dscm 1.58E-04 3.28E-04 1.67E-04 0.000 ng/dscm@7%O2 3.14E-04 5.43E-04 3.27E-04 0.000 ppm 1.01E-11 2.11E-11 1.07E-11 0.000 

### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000019 0.0000000042 0.0000000018 0.000 Elb/hr 1.56E-10 4.37E-10 1.49E-10 0.000 gr/dscf 8.73E-14 1.63E-13 8.78E-14 0.000 lb/mmBtuO2 3.42E-13 5.32E-13 3.39E-13 0.000 mg/dscm 2.00E-10 3.73E-10 2.01E-10 0.000 ng/dscm 2.00E-04 3.73E-04 2.01E-04 0.000 ng/dscm@7%O2 3.97E-04 6.17E-04 3.94E-04 0.000 ppm 1.23E-11 2.29E-11 1.24E-11 0.000 

### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000014 0.0000000036 0.0000000015 0.000 Elb/hr 1.15E-10 3.74E-10 1.24E-10 0.000 gr/dscf 6.43E-14 1.40E-13 7.32E-14 0.000 lb/mmBtuO2 2.52E-13 4.56E-13 2.83E-13 0.000 mg/dscm 1.47E-10 3.20E-10 1.67E-10 0.000 ng/dscm 1.47E-04 3.20E-04 1.67E-04 0.000 ng/dscm@7%O2 2.92E-04 5.30E-04 3.27E-04 0.000 ppm 9.45E-12 2.05E-11 1.07E-11 0.000



### Tuesday, February 22, 2011 Page 11 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Compound: 1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000018 0.0000000038 0.0000000017 0.000 Elb/hr 1.48E-10 3.95E-10 1.41E-10 0.000 gr/dscf 8.27E-14 1.47E-13 8.29E-14 0.000 lb/mmBtuO2 3.24E-13 4.81E-13 3.20E-13 0.000 mg/dscm 1.89E-10 3.37E-10 1.90E-10 0.000 ng/dscm 1.89E-04 3.37E-04 1.90E-04 0.000 ng/dscm@7%O2 3.75E-04 5.58E-04 3.72E-04 0.000 ppm 1.16E-11 2.08E-11 1.17E-11 0.000 

### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000017 0.0000000044 0.0000000018 0.000 Elb/hr 1.39E-10 4.57E-10 1.49E-10 0.000 gr/dscf 7.81E-14 1.71E-13 8.78E-14 0.000 lb/mmBtuO2 3.06E-13 5.57E-13 3.39E-13 0.000 mg/dscm 1.79E-10 3.91E-10 2.01E-10 0.000 ng/dscm 1.79E-04 3.91E-04 2.01E-04 0.000 ng/dscm@7%O2 3.55E-04 6.47E-04 3.94E-04 0.000 ppm 1.15E-11 2.51E-11 1.29E-11 0.000 

### Compound: 1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000017 0.0000000044 0.0000000018 0.000 Elb/hr 1.39E-10 4.57E-10 1.49E-10 0.000 gr/dscf 7.81E-14 1.71E-13 8.78E-14 0.000 lb/mmBtuO2 3.06E-13 5.57E-13 3.39E-13 0.000 mg/dscm 1.79E-10 3.91E-10 2.01E-10 0.000 ng/dscm 1.79E-04 3.91E-04 2.01E-04 0.000 ng/dscm@7%O2 3.55E-04 6.47E-04 3.94E-04 0.000 ppm 1.21E-11 2.63E-11 1.36E-11 0.000 

### Compound: 1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000018 0.0000000063 0.0000000019 0.000 Elb/hr 1.48E-10 6.55E-10 1.58E-10 0.000 gr/dscf 8.27E-14 2.44E-13 9.27E-14 0.000 lb/mmBtuO2 3.24E-13 7.98E-13 3.58E-13 0.000 mg/dscm 1.89E-10 5.59E-10 2.12E-10 0.000 ng/dscm 1.89E-04 5.59E-04 2.12E-04 0.000 ng/dscm@7%O2 3.75E-04 9.25E-04 4.15E-04 0.001 ppm 1.34E-11 3.95E-11 1.50E-11 0.000 

### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.0000000047 0.0000000093 0.0000000052 0.000 Elb/hr 3.85E-10 9.67E-10 4.31E-10 0.000



### Tuesday, February 22, 2011 Page 12 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 gr/dscf 2.16E-13 3.61E-13 2.54E-13 0.000 lb/mmBtuO2 8.47E-13 1.18E-12 9.80E-13 0.000 mg/dscm 4.94E-10 8.25E-10 5.80E-10 0.000 ng/dscm 4.94E-04 8.25E-04 5.80E-04 0.001 ng/dscm@7%O2 9.81E-04 1.37E-03 1.14E-03 0.001 ppm 3.00E-11 5.01E-11 3.52E-11 0.000 

### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.000000086 0.00000015 0.00000012 0.000 Elb/hr 7.05E-09 1.56E-08 9.95E-09 0.000 gr/dscf 3.95E-12 5.82E-12 5.85E-12 0.000 lb/mmBtuO2 1.55E-11 1.90E-11 2.26E-11 0.000 mg/dscm 9.05E-09 1.33E-08 1.34E-08 0.000 ng/dscm 9.05E-03 1.33E-02 1.34E-02 0.012 ng/dscm@7%O2 1.80E-02 2.20E-02 2.62E-02 0.022 ppm 0.000 

### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.00000048 0.00000073 0.00000062 0.000 Elb/hr 3.94E-08 7.59E-08 5.14E-08 0.000 gr/dscf 2.21E-11 2.83E-11 3.02E-11 0.000 lb/mmBtuO2 8.65E-11 9.25E-11 1.17E-10 0.000 mg/dscm 5.05E-08 6.48E-08 6.92E-08 0.000 ng/dscm 5.05E-02 6.48E-02 6.92E-02 0.062 ng/dscm@7%O2 1.00E-01 1.07E-01 1.35E-01 0.114 ppm 0.000 

### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.000000034 0.000000054 0.000000048 0.000 Elb/hr 2.79E-09 5.61E-09 3.98E-09 0.000 gr/dscf 1.56E-12 2.09E-12 2.34E-12 0.000 lb/mmBtuO2 6.12E-12 6.84E-12 9.05E-12 0.000 mg/dscm 3.58E-09 4.79E-09 5.36E-09 0.000 ng/dscm 3.58E-03 4.79E-03 5.36E-03 0.005 ng/dscm@7%O2 7.11E-03 7.93E-03 1.05E-02 0.009 ppm 2.38E-10 3.19E-10 3.57E-10 0.000 

### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.000000037 0.000000038 0.000000044 0.000 Elb/hr 3.03E-09 3.95E-09 3.65E-09 0.000 gr/dscf 1.70E-12 1.47E-12 2.15E-12 0.000 lb/mmBtuO2 6.66E-12 4.81E-12 8.29E-12 0.000 mg/dscm 3.89E-09 3.37E-09 4.91E-09 0.000 ng/dscm 3.89E-03 3.37E-03 4.91E-03 0.004 ng/dscm@7%O2 7.72E-03 5.58E-03 9.61E-03 0.008 ppm 0.000



### Tuesday, February 22, 2011 Page 13 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.0000015 0.0000021 0.0000019 0.000 Elb/hr 1.23E-07 2.18E-07 1.58E-07 0.000 gr/dscf 6.89E-11 8.14E-11 9.27E-11 0.000 lb/mmBtuO2 2.70E-10 2.66E-10 3.58E-10 0.000 mg/dscm 1.58E-07 1.86E-07 2.12E-07 0.000 ng/dscm 1.58E-01 1.86E-01 2.12E-01 0.185 ng/dscm@7%O2 3.14E-01 3.08E-01 4.15E-01 0.346 ppm 0.000 

### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.000000021 0.000000028 0.000000027 0.000 Elb/hr 1.72E-09 2.91E-09 2.24E-09 0.000 gr/dscf 9.65E-13 1.09E-12 1.32E-12 0.000 lb/mmBtuO2 3.78E-12 3.55E-12 5.09E-12 0.000 mg/dscm 2.21E-09 2.49E-09 3.01E-09 0.000 ng/dscm 2.21E-03 2.49E-03 3.01E-03 0.003 ng/dscm@7%O2 4.39E-03 4.12E-03 5.89E-03 0.005 ppm 0.000 

### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000017 0.0000000042 0.0000000017 0.000 Elb/hr 1.39E-10 4.37E-10 1.41E-10 0.000 gr/dscf 7.81E-14 1.63E-13 8.29E-14 0.000 lb/mmBtuO2 3.06E-13 5.32E-13 3.20E-13 0.000 mg/dscm 1.79E-10 3.73E-10 1.90E-10 0.000 ng/dscm 1.79E-04 3.73E-04 1.90E-04 0.000 ng/dscm@7%O2 3.55E-04 6.17E-04 3.72E-04 0.000 ppm 1.15E-11 2.39E-11 1.22E-11 0.000 

### Compound: 2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000022 0.000000006 0.0000000018 0.000 Elb/hr 1.80E-10 6.24E-10 1.49E-10 0.000 gr/dscf 1.01E-13 2.33E-13 8.78E-14 0.000 lb/mmBtuO2 3.96E-13 7.60E-13 3.39E-13 0.000 mg/dscm 2.31E-10 5.33E-10 2.01E-10 0.000 ng/dscm 2.31E-04 5.33E-04 2.01E-04 0.000 ng/dscm@7%O2 4.59E-04 8.82E-04 3.94E-04 0.001 ppm 1.63E-11 3.76E-11 1.42E-11 0.000 

### Compound: 2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.0000000021 0.0000000057 0.000000002 0.000 Elb/hr 1.72E-10 5.92E-10 1.66E-10 0.000



### Tuesday, February 22, 2011 Page 14 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 gr/dscf 9.65E-14 2.21E-13 9.75E-14 0.000 lb/mmBtuO2 3.78E-13 7.22E-13 3.77E-13 0.000 mg/dscm 2.21E-10 5.06E-10 2.23E-10 0.000 ng/dscm 2.21E-04 5.06E-04 2.23E-04 0.000 ng/dscm@7%O2 4.39E-04 8.37E-04 4.37E-04 0.001 ppm 1.65E-11 3.78E-11 1.67E-11 0.000 

### Compound: 2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000057 0.0000000048 0.0000000024 0.000 Elb/hr 4.67E-10 4.99E-10 1.99E-10 0.000 gr/dscf 2.62E-13 1.86E-13 1.17E-13 0.000 lb/mmBtuO2 1.03E-12 6.08E-13 4.52E-13 0.000 mg/dscm 6.00E-10 4.26E-10 2.68E-10 0.000 ng/dscm 6.00E-04 4.26E-04 2.68E-04 0.000 ng/dscm@7%O2 1.19E-03 7.05E-04 5.25E-04 0.001 ppm 4.71E-11 3.35E-11 2.11E-11 0.000 

### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.000000003 0.0000000058 0.0000000051 0.000 Elb/hr 2.46E-10 6.03E-10 4.23E-10 0.000 gr/dscf 1.38E-13 2.25E-13 2.49E-13 0.000 lb/mmBtuO2 5.40E-13 7.35E-13 9.61E-13 0.000 mg/dscm 3.16E-10 5.15E-10 5.69E-10 0.000 ng/dscm 3.16E-04 5.15E-04 5.69E-04 0.000 ng/dscm@7%O2 6.27E-04 8.52E-04 1.11E-03 0.001 ppm 0.000 

### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.000000004 0.0000000045 0.0000000066 0.000 Elb/hr 3.28E-10 4.68E-10 5.47E-10 0.000 gr/dscf 1.84E-13 1.75E-13 3.22E-13 0.000 lb/mmBtuO2 7.21E-13 5.70E-13 1.24E-12 0.000 mg/dscm 4.21E-10 3.99E-10 7.37E-10 0.000 ng/dscm 4.21E-04 3.99E-04 7.37E-04 0.001 ng/dscm@7%O2 8.36E-04 6.60E-04 1.44E-03 0.001 ppm 0.000 

### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.000000083 0.00000017 0.000000097 0.000 Elb/hr 6.81E-09 1.77E-08 8.04E-09 0.000 gr/dscf 3.81E-12 6.59E-12 4.73E-12 0.000 lb/mmBtuO2 1.50E-11 2.15E-11 1.83E-11 0.000 mg/dscm 8.73E-09 1.51E-08 1.08E-08 0.000 ng/dscm 8.73E-03 1.51E-02 1.08E-02 0.012 ng/dscm@7%O2 1.73E-02 2.50E-02 2.11E-02 0.021 ppm 0.000



### Tuesday, February 22, 2011 Page 15 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Compound: 3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.0000000026 0.0000000072 0.0000000034 0.000 Elb/hr 2.13E-10 7.48E-10 2.82E-10 0.000 gr/dscf 1.19E-13 2.79E-13 1.66E-13 0.000 lb/mmBtuO2 4.68E-13 9.12E-13 6.41E-13 0.000 mg/dscm 2.73E-10 6.39E-10 3.80E-10 0.000 ng/dscm 2.73E-04 6.39E-04 3.80E-04 0.000 ng/dscm@7%O2 5.42E-04 1.06E-03 7.44E-04 0.001 ppm 0.000 

### Compound: OCDD Average RunNumber 1 2 3 Mass_mg 0.000000012 0.0000000133 0.0000000093 0.000 Elb/hr 9.84E-10 1.38E-09 7.71E-10 0.000 gr/dscf 5.51E-13 5.16E-13 4.54E-13 0.000 lb/mmBtuO2 2.16E-12 1.68E-12 1.75E-12 0.000 mg/dscm 1.26E-09 1.18E-09 1.04E-09 0.000 ng/dscm 1.26E-03 1.18E-03 1.04E-03 0.001 ng/dscm@7%O2 2.50E-03 1.95E-03 2.04E-03 0.002 ppm 6.60E-11 6.17E-11 5.43E-11 0.000 

### Compound: OCDF Average RunNumber 1 2 3 Mass_mg 0.0000000032 0.0000000081 0.0000000034 0.000 Elb/hr 2.62E-10 8.42E-10 2.82E-10 0.000 gr/dscf 1.47E-13 3.14E-13 1.66E-13 0.000 lb/mmBtuO2 5.76E-13 1.03E-12 6.41E-13 0.000 mg/dscm 3.37E-10 7.19E-10 3.80E-10 0.000 ng/dscm 3.37E-04 7.19E-04 3.80E-04 0.000 ng/dscm@7%O2 6.69E-04 1.19E-03 7.44E-04 0.001 ppm 1.82E-11 3.90E-11 2.06E-11 0.000 

### Compound: Other HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000019 0.0000000035 0.0000000017 0.000 Elb/hr 1.56E-10 3.64E-10 1.41E-10 0.000 gr/dscf 8.73E-14 1.36E-13 8.29E-14 0.000 lb/mmBtuO2 3.42E-13 4.43E-13 3.20E-13 0.000 mg/dscm 2.00E-10 3.11E-10 1.90E-10 0.000 ng/dscm 2.00E-04 3.11E-04 1.90E-04 0.000 ng/dscm@7%O2 3.97E-04 5.15E-04 3.72E-04 0.000 ppm 1.13E-11 1.76E-11 1.07E-11 0.000 

### Compound: Other HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000022 0.0000000031 0.000000002 0.000 Elb/hr 1.80E-10 3.22E-10 1.66E-10 0.000



### Tuesday, February 22, 2011 Page 16 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 gr/dscf 1.01E-13 1.20E-13 9.75E-14 0.000 lb/mmBtuO2 3.96E-13 3.93E-13 3.77E-13 0.000 mg/dscm 2.31E-10 2.75E-10 2.23E-10 0.000 ng/dscm 2.31E-04 2.75E-04 2.23E-04 0.000 ng/dscm@7%O2 4.59E-04 4.55E-04 4.37E-04 0.000 ppm 1.36E-11 1.62E-11 1.31E-11 0.000 

### Compound: Other HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000067 0.0000000098 0.000000011 0.000 Elb/hr 5.49E-10 1.02E-09 9.12E-10 0.000 gr/dscf 3.08E-13 3.80E-13 5.36E-13 0.000 lb/mmBtuO2 1.21E-12 1.24E-12 2.07E-12 0.000 mg/dscm 7.05E-10 8.70E-10 1.23E-09 0.000 ng/dscm 7.05E-04 8.70E-04 1.23E-03 0.001 ng/dscm@7%O2 1.40E-03 1.44E-03 2.41E-03 0.002 ppm 4.34E-11 5.35E-11 7.55E-11 0.000 

### Compound: Other HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000016 0.0000000039 0.0000000016 0.000 Elb/hr 1.31E-10 4.05E-10 1.33E-10 0.000 gr/dscf 7.35E-14 1.51E-13 7.80E-14 0.000 lb/mmBtuO2 2.88E-13 4.94E-13 3.02E-13 0.000 mg/dscm 1.68E-10 3.46E-10 1.79E-10 0.000 ng/dscm 1.68E-04 3.46E-04 1.79E-04 0.000 ng/dscm@7%O2 3.34E-04 5.73E-04 3.50E-04 0.000 ppm 1.08E-11 2.22E-11 1.15E-11 0.000 

### Compound: Other PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000021 0.0000000044 0.000000003 0.000 Elb/hr 1.72E-10 4.57E-10 2.49E-10 0.000 gr/dscf 9.65E-14 1.71E-13 1.46E-13 0.000 lb/mmBtuO2 3.78E-13 5.57E-13 5.65E-13 0.000 mg/dscm 2.21E-10 3.91E-10 3.35E-10 0.000 ng/dscm 2.21E-04 3.91E-04 3.35E-04 0.000 ng/dscm@7%O2 4.39E-04 6.47E-04 6.56E-04 0.001 ppm 1.49E-11 2.63E-11 2.26E-11 0.000 

### Compound: Other PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000022 0.000000035 0.0000000069 0.000 Elb/hr 1.80E-10 3.64E-09 5.72E-10 0.000 gr/dscf 1.01E-13 1.36E-12 3.37E-13 0.000 lb/mmBtuO2 3.96E-13 4.43E-12 1.30E-12 0.000 mg/dscm 2.31E-10 3.11E-09 7.70E-10 0.000 ng/dscm 2.31E-04 3.11E-03 7.70E-04 0.001 ng/dscm@7%O2 4.59E-04 5.15E-03 1.51E-03 0.002 ppm 1.63E-11 2.19E-10 5.44E-11 0.000



### Tuesday, February 22, 2011 Page 17 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Compound: Other TCDD Average RunNumber 1 2 3 Mass_mg 0.0000000032 0.0000000057 0.0000000027 0.000 Elb/hr 2.62E-10 5.92E-10 2.24E-10 0.000 gr/dscf 1.47E-13 2.21E-13 1.32E-13 0.000 lb/mmBtuO2 5.76E-13 7.22E-13 5.09E-13 0.000 mg/dscm 3.37E-10 5.06E-10 3.01E-10 0.000 ng/dscm 3.37E-04 5.06E-04 3.01E-04 0.000 ng/dscm@7%O2 6.69E-04 8.37E-04 5.89E-04 0.001 ppm 2.51E-11 3.78E-11 2.25E-11 0.000 

### Compound: Other TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000087 0.0000000048 0.0000000024 0.000 Elb/hr 7.13E-10 4.99E-10 1.99E-10 0.000 gr/dscf 4.00E-13 1.86E-13 1.17E-13 0.000 lb/mmBtuO2 1.57E-12 6.08E-13 4.52E-13 0.000 mg/dscm 9.15E-10 4.26E-10 2.68E-10 0.000 ng/dscm 9.15E-04 4.26E-04 2.68E-04 0.001 ng/dscm@7%O2 1.82E-03 7.05E-04 5.25E-04 0.001 ppm 7.19E-11 3.35E-11 2.11E-11 0.000 

### Compound: Total Dioxins Average RunNumber 1 2 3 Mass_mg 0.0000000371 0.0000000622 0.0000000408 0.000 Elb/hr 3.04E-09 6.47E-09 3.38E-09 0.000 gr/dscf 1.70E-12 2.41E-12 1.99E-12 0.000 lb/mmBtuO2 6.68E-12 7.88E-12 7.69E-12 0.000 mg/dscm 3.90E-09 5.52E-09 4.55E-09 0.000 ng/dscm 3.90E-03 5.52E-03 4.55E-03 0.005 ng/dscm@7%O2 7.74E-03 9.13E-03 8.91E-03 0.009 ppm 0.000 

### Compound: Total Furans Average RunNumber 1 2 3 Mass_mg 0.0000000378 0.0000000942 0.0000000302 0.000 Elb/hr 3.10E-09 9.79E-09 2.50E-09 0.000 gr/dscf 1.74E-12 3.65E-12 1.47E-12 0.000 lb/mmBtuO2 6.81E-12 1.19E-11 5.69E-12 0.000 mg/dscm 3.98E-09 8.36E-09 3.37E-09 0.000 ng/dscm 3.98E-03 8.36E-03 3.37E-03 0.005 ng/dscm@7%O2 7.90E-03 1.38E-02 6.60E-03 0.009 ppm 0.000



### Location: Stack Exit - Method 25A 

### Compound: Total organic compounds (TOC) as Average Run 1-1 1-2 1-3 Elb/hr 1.12E+00 8.43E-01 2.50E-01 0.738


### Tuesday, February 22, 2011 Page 18 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 gr/dscf 3.35E-04 2.50E-04 7.29E-05 0.000 lb/mmBtuO2 9.01E-04 6.78E-04 2.02E-04 0.001 mg/dscm 7.66E-01 5.71E-01 1.67E-01 0.501 ppm 4.18E-01 3.12E-01 9.10E-02 0.274 ppm@7%O2 5.70E-01 4.29E-01 1.28E-01 0.376



### Location: Stack Exit - Method 26A Compound: Hydrogen Chloride Average RunNumber 1 2 3 Mass_mg 1 0.99 0.82 0.937 Elb/hr 6.44E-01 6.24E-01 5.20E-01 0.596 lb/mmBtuO2 1.50E-03 1.54E-03 1.28E-03 0.001 mg/dscm 8.85E-01 8.98E-01 7.47E-01 0.843 mg/dscm@7%O2 1.74E+00 1.79E+00 1.49E+00 1.673 

### Compound: Hydrogen Fluoride Average RunNumber 1 2 3 Mass_mg 0.11 0.11 0.11 0.110 Elb/hr 7.09E-02 6.93E-02 6.98E-02 0.070 lb/mmBtuO2 1.65E-04 1.71E-04 1.72E-04 0.000 mg/dscm 9.73E-02 9.98E-02 1.00E-01 0.099 mg/dscm@7%O2 1.92E-01 1.99E-01 1.99E-01 0.197



### Location: Stack Exit - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.3452 0.3122 0.29153 0.316 Elb/hr 9.89E-02 8.93E-02 8.31E-02 0.090 lb/mmBtuO2 7.81E-05 7.36E-05 7.13E-05 0.000 mg/dscm 7.23E-02 6.08E-02 6.00E-02 0.064 mg/dscm@7%O2 9.05E-02 8.54E-02 8.26E-02 0.086 

### Compound: Arsenic Average RunNumber 1 2 3 Mass_mg 0.0209 0.0177 0.00964 0.016 Elb/hr 5.99E-03 5.06E-03 2.75E-03 0.005 lb/mmBtuO2 4.73E-06 4.17E-06 2.36E-06 0.000 mg/dscm 4.38E-03 3.45E-03 1.99E-03 0.003 mg/dscm@7%O2 5.48E-03 4.84E-03 2.74E-03 0.004 

### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.00267 0.00241 0.00215 0.002 Elb/hr 7.65E-04 6.89E-04 6.13E-04 0.001 lb/mmBtuO2 6.04E-07 5.68E-07 5.26E-07 0.000 mg/dscm 5.59E-04 4.69E-04 4.43E-04 0.000 mg/dscm@7%O2 7.00E-04 6.58E-04 6.10E-04 0.001



### Tuesday, February 22, 2011 Page 19 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.00045 0.00043 0.000294 0.000 Elb/hr 1.29E-04 1.23E-04 8.38E-05 0.000 lb/mmBtuO2 1.02E-07 1.01E-07 7.19E-08 0.000 mg/dscm 9.42E-05 8.37E-05 6.06E-05 0.000 mg/dscm@7%O2 1.18E-04 1.18E-04 8.34E-05 0.000 

### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.07089 0.06335 0.02282 0.052 Elb/hr 2.03E-02 1.81E-02 6.50E-03 0.015 lb/mmBtuO2 1.60E-05 1.49E-05 5.58E-06 0.000 mg/dscm 1.48E-02 1.23E-02 4.70E-03 0.011 mg/dscm@7%O2 1.85E-02 1.73E-02 6.47E-03 0.014 

### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.20106 0.19105 0.15928 0.184 Elb/hr 5.76E-02 5.46E-02 4.54E-02 0.053 lb/mmBtuO2 4.55E-05 4.50E-05 3.89E-05 0.000 mg/dscm 4.21E-02 3.72E-02 3.28E-02 0.037 mg/dscm@7%O2 5.27E-02 5.22E-02 4.51E-02 0.050 

### Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 313.2 249.6 111.2 224.667 Elb/hr 8.98E+01 7.14E+01 3.17E+01 64.300 lb/mmBtuO2 7.08E-02 5.88E-02 2.72E-02 0.052 mg/dscm 6.56E+01 4.86E+01 2.29E+01 45.700 mg/dscm@7%O2 8.21E+01 6.82E+01 3.15E+01 60.600 

### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.06049 0.04958 0.02998 0.047 Elb/hr 1.73E-02 1.42E-02 8.54E-03 0.013 lb/mmBtuO2 1.37E-05 1.17E-05 7.33E-06 0.000 mg/dscm 1.27E-02 9.65E-03 6.17E-03 0.010 mg/dscm@7%O2 1.59E-02 1.35E-02 8.49E-03 0.013 

### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.4357 0.4518 0.2871 0.392 Elb/hr 1.25E-01 1.29E-01 8.18E-02 0.112 lb/mmBtuO2 9.86E-05 1.07E-04 7.02E-05 0.000 mg/dscm 9.13E-02 8.79E-02 5.91E-02 0.079 mg/dscm@7%O2 1.14E-01 1.23E-01 8.13E-02 0.106



### Tuesday, February 22, 2011 Page 20 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Compound: Nickel Average RunNumber 1 2 3 Mass_mg 3.1722 2.9712975 2.5953 2.913 Elb/hr 9.09E-01 8.50E-01 7.40E-01 0.833 lb/mmBtuO2 7.18E-04 7.00E-04 6.35E-04 0.001 mg/dscm 6.64E-01 5.78E-01 5.35E-01 0.592 mg/dscm@7%O2 8.31E-01 8.12E-01 7.36E-01 0.793 

### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.0108 0.0098 0.0056 0.009 Elb/hr 3.09E-03 2.80E-03 1.60E-03 0.002 lb/mmBtuO2 2.44E-06 2.31E-06 1.37E-06 0.000 mg/dscm 2.26E-03 1.91E-03 1.15E-03 0.002 mg/dscm@7%O2 2.83E-03 2.68E-03 1.58E-03 0.002



### Location: Stack Exit - Method 6C Compound: Sulfur Dioxide Average Run 1-1 1-2 1-3 Elb/hr 3.39E+02 3.48E+02 3.51E+02 346.000 lb/mmBtuO2 2.74E-01 2.80E-01 2.84E-01 0.279 mg/dscm 2.33E+02 2.36E+02 2.34E+02 234.333 mg/dscm@7%O2 3.18E+02 3.25E+02 3.29E+02 324.000 ppm 8.76E+01 8.85E+01 8.79E+01 88.000 ppm@7%O2 1.19E+02 1.22E+02 1.23E+02 121.333



### Location: Stack Exit - Method 6C 3 Compound: Sulfur Dioxide Average Run 3-1 3-2 3-3 Elb/hr 1.08E+02 1.08E+02 1.05E+02 107.000 lb/mmBtuO2 2.53E-01 2.59E-01 2.60E-01 0.257 mg/dscm 1.49E+02 1.51E+02 1.51E+02 150.333 mg/dscm@7%O2 2.93E+02 3.01E+02 3.01E+02 298.333 ppm 5.59E+01 5.66E+01 5.68E+01 56.433 ppm@7%O2 1.10E+02 1.13E+02 1.13E+02 112.000



### Location: Stack Exit - Method 7E Compound: Nitrogen oxides (NOx) Average Run 3-1 3-2 3-3 Elb/hr 8.07E+01 7.84E+01 7.48E+01 77.967 lb/mmBtuO2 1.88E-01 1.87E-01 1.85E-01 0.187 mg/dscm 1.11E+02 1.09E+02 1.08E+02 109.333 mg/dscm@7%O2 2.19E+02 2.17E+02 2.15E+02 217.000 ppm 5.80E+01 5.70E+01 5.62E+01 57.067 ppm@7%O2 1.14E+02 1.13E+02 1.12E+02 113.000



### Location: Stack Exit - OTM - 27/28
Tuesday, February 22, 2011 Page 21 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010

Process Run Data Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 76.8 136.4 76.7 96.633 Elb/hr 3.14E+01 5.63E+01 3.12E+01 39.633 gr/dscf 9.67E-03 1.65E-02 9.60E-03 0.012 lb/mmBtuO2 2.39E-02 4.57E-02 2.61E-02 0.032 mg/dscm 2.21E+01 3.77E+01 2.20E+01 27.267 ppm #Num!



### Tuesday, February 22, 2011 Page 22 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Process Run Data



### Run Name Value UOM Comments Target Value 1 Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 Run 1 M0010 Start 7/8/2010 16:24 End 7/8/2010 18:47 0



### 10Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 Run 1 M0011 7/8/2010 16:24 7/8/2010 18:45 0

11Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 Runs 1-4 M0031 7/8/2010 16:24 7/8/2010 18:25 0

12Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 Run 1 M6C (SO2) 7/8/2010 16:24 7/8/2010 18:47 0

13Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 Run 1 M10 (CO) 7/8/2010 16:24 7/8/2010 18:47 0

14Fuel Oil Firing Rate 7183 gal/hr SEW3 Group 1 Run 1 M25A (TOC as propane) 7/8/2010 16:24 7/8/2010 18:47 0



### 15Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 Run 2 M0010 7/8/2010 19:45 7/8/2010 22:01 0

16Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 Run 2 M0011 7/8/2010 19:48 7/8/2010 21:57 0

17Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 Runs 5-8 M0031 7/8/2010 19:45 7/8/2010 21:51 0

18Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 Run 2 M6C (SO2) 7/8/2010 19:45 7/8/2010 22:01 0

19Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 Run 2 M10 (CO) 7/8/2010 19:45 7/8/2010 22:01 0

Tuesday, February 22, 2011 Page 23 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 20Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 Run 2 M25A (TOC as propane) 7/8/2010 19:45 7/8/2010 22:01 0



### 21Fuel Oil Firing Rate 7332 gal/hr SEW3 Group 1 Run 3 M0010 7/9/2010 9:06 7/9/2010 11:15 0

22Fuel Oil Firing Rate 7332 gal/hr SEW3 Group 1 Run 3 M0011 7/9/2010 9:06 7/9/2010 11:14 0

23Fuel Oil Firing Rate 7227 gal/hr SEW3 Group 1 Runs 9-12 M0031 7/9/2010 9:12 7/9/2010 11:46 0

24Fuel Oil Firing Rate 7330 gal/hr SEW3 Group 1 Run 3 M6C (SO2) 7/9/2010 9:15 7/9/2010 11:15 0

25Fuel Oil Firing Rate 7330 gal/hr SEW3 Group 1 Run 3 M10 (CO) 7/9/2010 9:15 7/9/2010 11:15 0

26Fuel Oil Firing Rate 7330 gal/hr SEW3 Group 1 Run 3 M25A (TOC as propane) 7/9/2010 9:15 7/9/2010 11:15 0



### 27Fuel Oil Firing Rate 7182 gal/hr SEW3 Group 1 Run 1 M18 (CH4) 7/8/2010 18:50 7/8/2010 18:54 0

28Fuel Oil Firing Rate 7184 gal/hr SEW3 Group 1 Run 2 M18 (CH4) 7/8/2010 19:01 7/8/2010 19:04 0

29Fuel Oil Firing Rate 7185 gal/hr SEW3 Group 1 Run 3 M18 (CH4) 7/8/2010 19:09 7/8/2010 19:13 0

30Fuel Oil Firing Rate 2666 gal/hr SEW3 Group 2 Run 1 M23 7/7/2010 21:10 7/8/2010 7:05 0

31Fuel Oil Firing Rate 4584 gal/hr SEW3 Group 2 Run 2 M23 7/8/2010 23:10 7/9/2010 7:28 0

Tuesday, February 22, 2011 Page 24 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 32Fuel Oil Firing Rate 2543 gal/hr SEW3 Group 2 Run 3 M23 7/9/2010 12:58 7/9/2010 21:06 0

33Fuel Oil Firing Rate 2538 gal/hr SEW3 Group 3 Run 1 M26A 7/9/2010 12:58 7/9/2010 14:07 0

34Fuel Oil Firing Rate 2539 gal/hr SEW3 Group 3 Run 1 M6C (SO2) 7/9/2010 12:59 7/9/2010 14:09 0

35Fuel Oil Firing Rate 2539 gal/hr SEW3 Group 3 Run 1 M7E (NOx) 7/9/2010 12:59 7/9/2010 14:09 0

36Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 Run 2 M26A 7/9/2010 14:40 7/9/2010 15:51 0

37Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 Run 2 M6C (SO2) 7/9/2010 14:42 7/9/2010 15:42 0

38Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 Run 2 M7E (NOx) 7/9/2010 14:42 7/9/2010 15:42 0

39Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 Run 3 M26A 7/9/2010 16:10 7/9/2010 17:17 0

4 Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 Run 3 M6C (SO2) 7/9/2010 16:12 7/9/2010 17:11 0

40Fuel Oil Firing Rate 2544 gal/hr SEW3 Group 3 Run 3 M7E (NOx) 7/9/2010 16:12 7/9/2010 17:11 0

41Fuel Oil Firing Rate 7702 gal/hr SEW3 Group 4 Run 1 M29 7/6/2010 15:58 7/6/2010 21:57 0

42Fuel Oil Firing Rate 7701 gal/hr SEW3 Group 4 Run 1 OTM027/028 7/6/2010 16:00 7/6/2010 22:05 0



### Tuesday, February 22, 2011 Page 25 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 43Fuel Oil Firing Rate 7717 gal/hr SEW3 Group 4 Run 1 M30B 7/6/2010 14:22 7/6/2010 20:22 0

44Fuel Oil Firing Rate 7220 gal/hr SEW3 Group 4 Run 2 M29 7/7/2010 13:00 7/7/2010 18:33 0

5 Fuel Oil Firing Rate 7220 gal/hr SEW3 Group 4 Run 2 OTM027/028 7/7/2010 13:00 7/7/2010 19:08 0



### 6 Fuel Oil Firing Rate 7220 gal/hr SEW3 Group 4 Run 2 M30B 7/7/2010 13:04 7/7/2010 19:04 0

7 Fuel Oil Firing Rate 7180 gal/hr SEW3 Group 4 Run 3 M29 7/8/2010 8:30 7/8/2010 14:07 0

8 Fuel Oil Firing Rate 7180 gal/hr SEW3 Group 4 Run 3 OTM027/028 7/8/2010 8:30 7/8/2010 14:17 0



### 9 Fuel Oil Firing Rate 7180 gal/hr SEW3 Group 4 Run 3 M30B 7/8/2010 8:31 7/8/2010 14:31 0

1 Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 1 M0010 Start 7/8/2010 16:24 End 7/8/2010 18:47 0

10Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 1 M0011 7/8/2010 16:24 7/8/2010 18:45 0

11Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Runs 1-4 M0031 7/8/2010 16:24 7/8/2010 18:25 0

12Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 1 M6C (SO2) 7/8/2010 16:24 7/8/2010 18:47 0

13Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 1 M10 (CO) 7/8/2010 16:24 7/8/2010 18:47 0

Tuesday, February 22, 2011 Page 26 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 14Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 1 M25A (TOC as propane) 7/8/2010 16:24 7/8/2010 18:47 0



### 15Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 2 M0010 7/8/2010 19:45 7/8/2010 22:01 0

16Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 2 M0011 7/8/2010 19:48 7/8/2010 21:57 0

17Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Runs 5-8 M0031 7/8/2010 19:45 7/8/2010 21:51 0

18Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 2 M6C (SO2) 7/8/2010 19:45 7/8/2010 22:01 0

19Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 2 M10 (CO) 7/8/2010 19:45 7/8/2010 22:01 0

20Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 2 M25A (TOC as propane) 7/8/2010 19:45 7/8/2010 22:01 0



### 21Unit Gross Electrical Output 104 Mwe SEW3 Group 1 Run 3 M0010 7/9/2010 9:06 7/9/2010 11:15 0

22Unit Gross Electrical Output 104 Mwe SEW3 Group 1 Run 3 M0011 7/9/2010 9:06 7/9/2010 11:14 0

23Unit Gross Electrical Output 102 Mwe SEW3 Group 1 Runs 9-12 M0031 7/9/2010 9:12 7/9/2010 11:46 0

24Unit Gross Electrical Output 104 Mwe SEW3 Group 1 Run 3 M6C (SO2) 7/9/2010 9:15 7/9/2010 11:15 0

25Unit Gross Electrical Output 104 Mwe SEW3 Group 1 Run 3 M10 (CO) 7/9/2010 9:15 7/9/2010 11:15 0

Tuesday, February 22, 2011 Page 27 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 26Unit Gross Electrical Output 104 Mwe SEW3 Group 1 Run 3 M25A (TOC as propane) 7/9/2010 9:15 7/9/2010 11:15 0



### 27Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 1 M18 (CH4) 7/8/2010 18:50 7/8/2010 18:54 0

28Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 2 M18 (CH4) 7/8/2010 19:01 7/8/2010 19:04 0

29Unit Gross Electrical Output 101 Mwe SEW3 Group 1 Run 3 M18 (CH4) 7/8/2010 19:09 7/8/2010 19:13 0

30Unit Gross Electrical Output 30 Mwe SEW3 Group 2 Run 1 M23 7/7/2010 21:10 7/8/2010 7:05 0

31Unit Gross Electrical Output 60 Mwe SEW3 Group 2 Run 2 M23 7/8/2010 23:10 7/9/2010 7:28 0

32Unit Gross Electrical Output 29 Mwe SEW3 Group 2 Run 3 M23 7/9/2010 12:58 7/9/2010 21:06 0

33Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 1 M26A 7/9/2010 12:58 7/9/2010 14:07 0

34Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 1 M6C (SO2) 7/9/2010 12:59 7/9/2010 14:09 0

35Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 1 M7E (NOx) 7/9/2010 12:59 7/9/2010 14:09 0

36Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 2 M26A 7/9/2010 14:40 7/9/2010 15:51 0

37Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 2 M6C (SO2) 7/9/2010 14:42 7/9/2010 15:42 0



### Tuesday, February 22, 2011 Page 28 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 38Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 2 M7E (NOx) 7/9/2010 14:42 7/9/2010 15:42 0

39Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 3 M26A 7/9/2010 16:10 7/9/2010 17:17 0

4 Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 3 M6C (SO2) 7/9/2010 16:12 7/9/2010 17:11 0

40Unit Gross Electrical Output 29 Mwe SEW3 Group 3 Run 3 M7E (NOx) 7/9/2010 16:12 7/9/2010 17:11 0

41Unit Gross Electrical Output 108 Mwe SEW3 Group 4 Run 1 M29 7/6/2010 15:58 7/6/2010 21:57 0

42Unit Gross Electrical Output 108 Mwe SEW3 Group 4 Run 1 OTM027/028 7/6/2010 16:00 7/6/2010 22:05 0

43Unit Gross Electrical Output 108 Mwe SEW3 Group 4 Run 1 M30B 7/6/2010 14:22 7/6/2010 20:22 0

44Unit Gross Electrical Output 102 Mwe SEW3 Group 4 Run 2 M29 7/7/2010 13:00 7/7/2010 18:33 0

5 Unit Gross Electrical Output 102 Mwe SEW3 Group 4 Run 2 OTM027/028 7/7/2010 13:00 7/7/2010 19:08 0



### 6 Unit Gross Electrical Output 102 Mwe SEW3 Group 4 Run 2 M30B 7/7/2010 13:04 7/7/2010 19:04 0

7 Unit Gross Electrical Output 100 Mwe SEW3 Group 4 Run 3 M29 7/8/2010 8:30 7/8/2010 14:07 0

8 Unit Gross Electrical Output 100 Mwe SEW3 Group 4 Run 3 OTM027/028 7/8/2010 8:30 7/8/2010 14:17 0

Tuesday, February 22, 2011 Page 29 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 9 Unit Gross Electrical Output 100 Mwe SEW3 Group 4 Run 3 M30B 7/8/2010 8:31 7/8/2010 14:31 0

1 Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 1 M0010 Start 7/8/2010 16:24 End 7/8/2010 18:47 0



### 10Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 1 M0011 7/8/2010 16:24 7/8/2010 18:45 0

11Unit Net Electric Generation 94 MWh SEW3 Group 1 Runs 1-4 M0031 7/8/2010 16:24 7/8/2010 18:25 0

12Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 1 M6C (SO2) 7/8/2010 16:24 7/8/2010 18:47 0

13Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 1 M10 (CO) 7/8/2010 16:24 7/8/2010 18:47 0

14Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 1 M25A (TOC as propane) 7/8/2010 16:24 7/8/2010 18:47 0



### 15Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 2 M0010 7/8/2010 19:45 7/8/2010 22:01 0

16Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 2 M0011 7/8/2010 19:48 7/8/2010 21:57 0

17Unit Net Electric Generation 94 MWh SEW3 Group 1 Runs 5-8 M0031 7/8/2010 19:45 7/8/2010 21:51 0

18Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 2 M6C (SO2) 7/8/2010 19:45 7/8/2010 22:01 0

19Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 2 M10 (CO) 7/8/2010 19:45 7/8/2010 22:01 0

Tuesday, February 22, 2011 Page 30 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 20Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 2 M25A (TOC as propane) 7/8/2010 19:45 7/8/2010 22:01 0



### 21Unit Net Electric Generation 97 MWh SEW3 Group 1 Run 3 M0010 7/9/2010 9:06 7/9/2010 11:15 0

22Unit Net Electric Generation 97 MWh SEW3 Group 1 Run 3 M0011 7/9/2010 9:06 7/9/2010 11:14 0

23Unit Net Electric Generation 96 MWh SEW3 Group 1 Runs 9-12 M0031 7/9/2010 9:12 7/9/2010 11:46 0

24Unit Net Electric Generation 97 MWh SEW3 Group 1 Run 3 M6C (SO2) 7/9/2010 9:15 7/9/2010 11:15 0

25Unit Net Electric Generation 97 MWh SEW3 Group 1 Run 3 M10 (CO) 7/9/2010 9:15 7/9/2010 11:15 0

26Unit Net Electric Generation 97 MWh SEW3 Group 1 Run 3 M25A (TOC as propane) 7/9/2010 9:15 7/9/2010 11:15 0



### 27Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 1 M18 (CH4) 7/8/2010 18:50 7/8/2010 18:54 0

28Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 2 M18 (CH4) 7/8/2010 19:01 7/8/2010 19:04 0

29Unit Net Electric Generation 94 MWh SEW3 Group 1 Run 3 M18 (CH4) 7/8/2010 19:09 7/8/2010 19:13 0

30Unit Net Electric Generation 28 MWh SEW3 Group 2 Run 1 M23 7/7/2010 21:10 7/8/2010 7:05 0

31Unit Net Electric Generation 56 MWh SEW3 Group 2 Run 2 M23 7/8/2010 23:10 7/9/2010 7:28 0

Tuesday, February 22, 2011 Page 31 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 32Unit Net Electric Generation 27 MWh SEW3 Group 2 Run 3 M23 7/9/2010 12:58 7/9/2010 21:06 0

33Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 1 M26A 7/9/2010 12:58 7/9/2010 14:07 0

34Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 1 M6C (SO2) 7/9/2010 12:59 7/9/2010 14:09 0

35Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 1 M7E (NOx) 7/9/2010 12:59 7/9/2010 14:09 0

36Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 2 M26A 7/9/2010 14:40 7/9/2010 15:51 0

37Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 2 M6C (SO2) 7/9/2010 14:42 7/9/2010 15:42 0

38Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 2 M7E (NOx) 7/9/2010 14:42 7/9/2010 15:42 0

39Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 3 M26A 7/9/2010 16:10 7/9/2010 17:17 0

4 Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 3 M6C (SO2) 7/9/2010 16:12 7/9/2010 17:11 0

40Unit Net Electric Generation 27 MWh SEW3 Group 3 Run 3 M7E (NOx) 7/9/2010 16:12 7/9/2010 17:11 0

41Unit Net Electric Generation 101 MWh SEW3 Group 4 Run 1 M29 7/6/2010 15:58 7/6/2010 21:57 0

42Unit Net Electric Generation 101 MWh SEW3 Group 4 Run 1 OTM027/028 7/6/2010 16:00 7/6/2010 22:05 0



### Tuesday, February 22, 2011 Page 32 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010

APCD Run Data

Process Lab Run Data 43Unit Net Electric Generation 102 MWh SEW3 Group 4 Run 1 M30B 7/6/2010 14:22 7/6/2010 20:22 0

44Unit Net Electric Generation 95 MWh SEW3 Group 4 Run 2 M29 7/7/2010 13:00 7/7/2010 18:33 0

5 Unit Net Electric Generation 95 MWh SEW3 Group 4 Run 2 OTM027/028 7/7/2010 13:00 7/7/2010 19:08 0



### 6 Unit Net Electric Generation 95 MWh SEW3 Group 4 Run 2 M30B 7/7/2010 13:04 7/7/2010 19:04 0

7 Unit Net Electric Generation 94 MWh SEW3 Group 4 Run 3 M29 7/8/2010 8:30 7/8/2010 14:07 0

8 Unit Net Electric Generation 94 MWh SEW3 Group 4 Run 3 OTM027/028 7/8/2010 8:30 7/8/2010 14:17 0



### 9 Unit Net Electric Generation 94 MWh SEW3 Group 4 Run 3 M30B 7/8/2010 8:31 7/8/2010 14:31 0

1 Heat Input 0 Million Btus/million BTU using O2 0

Run Name Value UOM Comments Target Value 1 None 0 0


### 1 0 0
1 0 0

Run Name ValueUOM Comments 1 Fuel Higher Heating Value 0 Btu/lb 

### 1 Fuel Moisture 0 % 1 Fuel Mercury Content 0 ppm 1 Fuel Cadmium Content 0 ppm 1 Ultimate/Proximate Analysis 0



### Tuesday, February 22, 2011 Page 33 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 1 Fuel Nickel Content 0 ppm 

### 1 Fuel Arsenic Content 0 ppm 1 Fuel Chromium Content 0 ppm 1 Fuel Beryllium Content 0 ppm 1 Fuel Lead Content 0 ppm 

### 1 Fuel Manganese Content 0 ppm 1 Fuel Chlorine Content 0 ppm 1 Fuel Fluorine Content 0 ppm



### Tuesday, February 22, 2011 Page 34 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010 Sampling / Stack Data Results Detail



### LocationStack Exit - Method 0011 Average Run Number 1 2 3 Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:48:00 PM 9:06:00 AM Run Finish Time 6:45:00 PM9:57:00 PM11:14:00 AM Net Traversing Points 24 24 24 Net Run Time, minutes 120 120 120 Nozzle Diameter, inches 0.217 0.217 0.219 0.218 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9906 0.9906 0.9906 0.991 Barometric Pressure, inches of Mercury 29.91 29.915 29.89 29.905 Average Orifice Meter Differential, inches H2O 1.40 1.46 1.47 1.443 Dry Gas Meter Volume Sampled, cubic feet 78.180 78.792 81.281 79.418 Average Dry Gas Meter Temperature, °F 104.81 99.10 98.77 100.893 Dry Gas Meter Volume Sampled, dscf 72.623 73.962 76.282 74.289 Total Moisture Liquid collected, g 139.8 150.4 145.6 145.267 Volume of Water Vapor, standard cubic feet 6.58 7.08 6.85 6.837 Moisture Content of Stack Gas, % 8.31 8.74 8.24 8.430 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9169 0.9126 0.9176 0.916 Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Carbon Monoxide & Nitrogen, % 81.7 81.6 81.6 81.633 Fuel Factor 1.34 1.33 1.34 Dry Molecular Weight, lb/lb-Mole 29.64 29.65 29.62 29.637 Wet Molecular weight, lb/lb-Mole 28.67 28.63 28.66 28.653 Flue Gas Static Pressure, inches of H2O 0.2 0.2 0.2 0.200 Absolute Flue Gas Pressure, inches of Mercury 29.92 29.93 29.90 29.917 Average Stack Gas Temperature, °F 258.92 256.92 260.50 258.780 Average Velocity Head, inches of H2O 0.8376328350 823850.891715552

4967080.888728642

560459 0.873
Average Stack Gas Velocity, feet/second 60.17 62.03 62.08 61.427 Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812 Dry Volumetric Flow Rate, dry scfm 388,522.3 399,899.8 400,014.1396,145.400 Actual Wet Volumetric Flue Gas Flow Rate, acfm 576,953.3 594,788.3 595,267.7589,003.100 Percent Isokinetic of Sampling Rate, % 96.9 95.9 97.1 96.633 Percent Excess Air, % 98.4 100.5 104.3 101.067 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.263 14.263 14.263 Rectangular Duct Width, inches 151.7 151.7 151.7 Rectangular Duct Length, inches 151.7 151.7 151.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 35 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 10 Average Run Number 1-1 1-2 1-3 Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:45:00 PM 9:15:00 AM Run Finish Time 6:47:00 PM10:01:00 PM11:15:00 AM Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Fuel Factor 1.34 1.33 1.34 Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5394,229.267 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 8.85 9.02 8.07 8.647 Analyzer Make Thermo Scientific Thermo

Scientific Thermo

Scientific Analyzer Model 48i 48i 48i Analyzer Serial Number CMO8460052CMO846005 2CMO846005

2 Operating Range 99.5 99.5 99.5 99.500 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 110 110 113 111.000 Calibration Pre Zero Cylinder ID Nitrogen-CONitrogen-CONitrogen-CO Calibration Pre Zero Cylinder Instrument Response 0.341 0.048 0.341 0.243 Calibration Pre Zero Cylinder Bias 0.34 0.05 0.32 0.237 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID ALM00000- CO-MidALM00000-

CO-MidALM00000-

CO-Mid Calibration Pre High Cylinder Instrument Response 48.852 49.047 49.951 49.283 Calibration Pre High Cylinder Bias -1.35 -1.15 -0.71 -1.070 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-CONitrogen-CONitrogen-CO Calibration Post Zero Cylinder Instrument Response 0.048 0.146 0.097 0.097 Calibration Post Zero Cylinder Bias 0.05 0.15 0.07 0.090 Calibration Post Zero Cylinder Drift 0.29 0.1 0.25 0.213 Calibration Post High Cylinder ID ALM00000- CO-MidALM00000-

CO-MidALM00000-

CO-Mid Calibration Post High Cylinder Instrument Response 49.047 49.536 49.926 49.503 Calibration Post High Cylinder Bias -1.15 -0.66 -0.74 -0.850 Calibration Post High Cylinder Drift 0.2 0.49 0.03 0.240 Cavg 0.9 0.8 -0.1 0.533 Cavg Units ppmvd ppmvd ppmvd Cgas 0.725 0.7159 0 0.480 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 36 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 23 Average Run Number 1 2 3 Test Date 7/7/2010 7/8/2010 7/9/2010 Run Start Time 7:04:00 AM7:28:00 AM12:58:00 PM Run Finish Time 9:10:00 PM11:10:00 PM 9:06:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 576 480 480 Nozzle Diameter, inches 0.288 0.288 0.316 0.297 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988 Barometric Pressure, inches of Mercury 29.9 29.915 29.815 29.877 Average Orifice Meter Differential, inches H2O 1.14 2.51 1.52 1.723 Dry Gas Meter Volume Sampled, cubic feet 354.728 419.684 334.505 369.639 Average Dry Gas Meter Temperature, °F 92.33 93.58 91.71 92.540 Dry Gas Meter Volume Sampled, dscf 335.816 397.942 316.423 350.060 Total Moisture Liquid collected, g 516.5 643.8 482.4 547.567 Volume of Water Vapor, standard cubic feet 24.31 30.30 22.71 25.773 Moisture Content of Stack Gas, % 6.75 7.08 6.70 6.843 Moisture Saturation at Stack Gas Temperature, % 97.13 100.00 93.65 96.927 Dry Mole Fraction 0.9325 0.9292 0.933 0.932 Carbon Dioxide, % 5.3 6.4 5.1 5.600 Oxygen, % 13.9 12.5 13.8 13.400 Carbon Monoxide & Nitrogen, % 80.8 81.1 81.1 81.000 Fuel Factor 1.32 1.31 1.39 Dry Molecular Weight, lb/lb-Mole 29.40 29.52 29.37 29.430 Wet Molecular weight, lb/lb-Mole 28.63 28.70 28.61 28.647 Flue Gas Static Pressure, inches of H2O 0.26 0.28 -0.09 0.150 Absolute Flue Gas Pressure, inches of Mercury 29.92 29.94 29.81 29.890 Average Stack Gas Temperature, °F 210.54 233.54 208.54 217.540 Average Velocity Head, inches of H2O 0.2166688140 805060.509863524

5279340.196367798

633064 0.308
Average Stack Gas Velocity, feet/second 29.57 46.07 28.17 34.603 Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812 Dry Volumetric Flow Rate, dry scfm 208,194.9 312,709.2 198,306.1239,736.733 Actual Wet Volumetric Flue Gas Flow Rate, acfm 283,538.5 441,752.3 270,114.2331,801.667 Percent Isokinetic of Sampling Rate, % 98.9 93.7 97.5 96.700 Percent Excess Air, % 187.0 140.3 181.3 169.533 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.263 14.263 14.263 Rectangular Duct Width, inches 151.7 151.7 151.7 Rectangular Duct Length, inches 151.7 151.7 151.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 37 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 25A Average Run Number 1-1 1-2 1-3 Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:45:00 PM 9:15:00 AM Run Finish Time 6:47:00 PM10:01:00 PM11:15:00 AM Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Fuel Factor 1.34 1.33 1.34 Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5394,229.267 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 8.31 8.94 8.24 8.497 Analyzer Make Thermo Electron Thermo

Electron Thermo

Electron Analyzer Model 51C 51C 51C Analyzer Serial Number 032720220303272022030327202203327,202,203 .000 Operating Range 10 10 10 10.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 111 111 220 147.333 Calibration Pre Zero Cylinder ID Nitrogen-THC NitrogenTHC NitrogenTHC Calibration Pre Zero Cylinder Instrument Response -0.034 0.002 0.012 -0.007 Calibration Pre Zero Cylinder Bias -0.34 0.02 0.08 -0.080 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID BBB00000- THC-LowBBB00000-

THC-Low BBB00000-

THC-Low Calibration Pre High Cylinder Instrument Response 2.98 2.961 3.051 2.997 Calibration Pre High Cylinder Bias -1.2 -1.39 -0.59 -1.060 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-THC NitrogenTHC NitrogenTHC Calibration Post Zero Cylinder Instrument Response 0.002 -0.222 0.004 -0.072 Calibration Post Zero Cylinder Bias 0.02 -2.22 0 -0.733 Calibration Post Zero Cylinder Drift 0.36 2.24 0.08 0.893 Calibration Post High Cylinder ID BBB00000- THC-LowBBB00000-

THC-Low BBB00000-

THC-Low Calibration Post High Cylinder Instrument Response 2.961 2.79 3.032 2.928 Calibration Post High Cylinder Bias -1.39 -3.1 -0.78 -1.757 Calibration Post High Cylinder Drift 0.19 1.71 0.19 0.697 Cavg 0.4 0.2 0.1 0.233 Cavg Units ppmvd ppmvd ppmvd Cgas 0.4179 0.3115 0.091 0.273 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 38 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 26A Average Run Number 1 2 3 Test Date 7/9/2010 7/9/2010 7/9/2010 Run Start Time 12:58:00 PM2:40:00 PM 4:10:00 PM Run Finish Time 2:07:00 PM3:51:00 PM 5:17:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 60 60 60 Nozzle Diameter, inches 0.318 0.318 0.318 0.318 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9906 0.9906 0.9906 0.991 Barometric Pressure, inches of Mercury 29.84 29.8 29.765 29.802 Average Orifice Meter Differential, inches H2O 1.68 1.55 1.56 1.597 Dry Gas Meter Volume Sampled, cubic feet 42.643 41.841 41.816 42.100 Average Dry Gas Meter Temperature, °F 99.60 101.90 102.98 101.493 Dry Gas Meter Volume Sampled, dscf 39.915 38.939 38.797 39.217 Total Moisture Liquid collected, g 92.2 88.6 84.6 88.467 Volume of Water Vapor, standard cubic feet 4.34 4.17 3.98 4.163 Moisture Content of Stack Gas, % 9.81 9.67 9.30 9.593 Moisture Saturation at Stack Gas Temperature, % 92.57 88.94 88.27 89.927 Dry Mole Fraction 0.9019 0.9033 0.907 0.904 Carbon Dioxide, % 5.162 5.198 5.185 5.182 Oxygen, % 13.841 13.918 13.929 13.896 Carbon Monoxide & Nitrogen, % 80.997 80.884 80.886 80.922 Fuel Factor 1.37 1.34 1.34 Dry Molecular Weight, lb/lb-Mole 29.38 29.39 29.39 29.387 Wet Molecular weight, lb/lb-Mole 28.26 28.29 28.33 28.293 Flue Gas Static Pressure, inches of H2O -0.09 -0.09 -0.09 -0.090 Absolute Flue Gas Pressure, inches of Mercury 29.83 29.79 29.76 29.793 Average Stack Gas Temperature, °F 208.00 205.96 205.54 206.500 Average Velocity Head, inches of H2O 0.1991035484 111540.180662510

7190940.180474966

099066 0.187
Average Stack Gas Velocity, feet/second 28.52 27.13 27.11 27.587 Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812 Dry Volumetric Flow Rate, dry scfm 194,364.8 185,497.1 186,049.5188,637.133 Actual Wet Volumetric Flue Gas Flow Rate, acfm 273,470.3 260,142.0 259,950.2264,520.833 Percent Isokinetic of Sampling Rate, % 99.2 101.4 100.7 100.433 Percent Excess Air, % 183.5 187.2 187.6 186.100 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.263 14.263 14.263 Rectangular Duct Width, inches 151.7 151.7 151.7 Rectangular Duct Length, inches 151.7 151.7 151.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 39 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 29 Average Run Number 1 2 3 Test Date 7/6/2010 7/7/2010 7/8/2010 Run Start Time 3:58:00 PM1:00:00 PM 8:30:00 AM Run Finish Time 9:27:00 PM6:33:00 PM 2:07:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 300 300 300 Nozzle Diameter, inches 0.213 0.215 0.214 0.214 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9882 0.9882 0.9882 0.988 Barometric Pressure, inches of Mercury 29.855 29.89 29.935 29.893 Average Orifice Meter Differential, inches H2O 1.10 1.25 1.09 1.147 Dry Gas Meter Volume Sampled, cubic feet 185.800 196.161 183.044 188.335 Average Dry Gas Meter Temperature, °F 115.17 105.25 98.71 106.377 Dry Gas Meter Volume Sampled, dscf 168.639 181.447 171.485 173.857 Total Moisture Liquid collected, g 327.9 330.5 322.3 326.900 Volume of Water Vapor, standard cubic feet 15.43 15.56 15.17 15.387 Moisture Content of Stack Gas, % 8.38 7.90 8.13 8.137 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9162 0.921 0.9187 0.919 Carbon Dioxide, % 8.5 7.3 7.5 7.767 Oxygen, % 9.8 11 10.8 10.533 Carbon Monoxide & Nitrogen, % 81.7 81.7 81.7 81.700 Fuel Factor 1.31 1.36 1.35 Dry Molecular Weight, lb/lb-Mole 29.75 29.61 29.63 29.663 Wet Molecular weight, lb/lb-Mole 28.77 28.69 28.68 28.713 Flue Gas Static Pressure, inches of H2O -0.31 0.2 -0.2 -0.103 Absolute Flue Gas Pressure, inches of Mercury 29.83 29.90 29.92 29.883 Average Stack Gas Temperature, °F 294.96 271.29 259.42 275.223 Average Velocity Head, inches of H2O 0.7840257178 189820.861641761

6421790.755544851

668207 0.800
Average Stack Gas Velocity, feet/second 59.64 61.55 57.15 59.447 Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812 Dry Volumetric Flow Rate, dry scfm 365,334.1 392,195.1 369,489.4375,672.867 Actual Wet Volumetric Flue Gas Flow Rate, acfm 571,871.3 590,185.7 547,995.3570,017.433 Percent Isokinetic of Sampling Rate, % 99.4 97.8 99.0 98.733 Percent Excess Air, % 83.3 104.1 100.3 95.900 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.263 14.263 14.263 Rectangular Duct Width, inches 151.7 151.7 151.7 Rectangular Duct Length, inches 151.7 151.7 151.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 40 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 6C Average Run Number 1-1 1-2 1-3 Test Date 7/8/2010 7/8/2010 7/9/2010 Run Start Time 4:24:00 PM7:45:00 PM 9:15:00 AM Run Finish Time 6:47:00 PM10:01:00 PM11:15:00 AM Carbon Dioxide, % 7.6 7.6 7.4 7.533 Oxygen, % 10.7 10.8 11 10.833 Fuel Factor 1.34 1.33 1.34 Dry Volumetric Flow Rate, dry scfm 388586.9 394022.4 400078.5394,229.267 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 8.85 9.02 8.07 8.647 Analyzer Make Ametek Ametek Ametek Analyzer Model 921CE 921CE 921CE Analyzer Serial Number AE-921-6434 AE-921- 6434AE-921-6434
Operating Range 201 201 201 201.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 3 3 111 39.000 Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Pre Zero Cylinder Instrument Response 1.77 1.279 1.475 1.508 Calibration Pre Zero Cylinder Bias 1.12 0.88 1.08 1.027 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID ALM045659- SO2-MidALM045659

-SO2-MidALM045659-

SO2-Mid Calibration Pre High Cylinder Instrument Response 99.175 96.224 95.732 97.044 Calibration Pre High Cylinder Bias 0 -1.47 -3.38 -1.617 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Post Zero Cylinder Instrument Response 1.279 2.066 3.443 2.263 Calibration Post Zero Cylinder Bias 0.88 1.27 2.06 1.403 Calibration Post Zero Cylinder Drift 0.24 0.39 0.98 0.537 Calibration Post High Cylinder ID ALM045659- SO2-MidALM045659

-SO2-MidALM045659-

SO2-Mid Calibration Post High Cylinder Instrument Response 96.224 96.42 95.732 96.125 Calibration Post High Cylinder Bias -1.47 -1.37 -3.38 -2.073 Calibration Post High Cylinder Drift 1.479.999999999 99999E-02 0 0.523
Cavg 86.6 86.3 85.3 86.067 Cavg Units ppmvd ppmvd ppmvd Cgas 87.5745 88.5173 87.9275 88.006 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 41 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 6C 3 Average Run Number 3-1 3-2 3-3 Test Date 7/9/2010 7/9/2010 7/9/2010 Run Start Time 12:59:00 PM2:42:00 PM 4:12:00 PM Run Finish Time 2:09:00 PM3:42:00 PM 5:11:00 PM Carbon Dioxide, % 5.162 5.198 5.185 5.182 Oxygen, % 13.841 13.918 13.929 13.896 Fuel Factor 1.37 1.34 1.34 Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775190,654.633 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 5.5 5.5 5.5 5.500 Analyzer Make Ametek Ametek Ametek Analyzer Model 921CE 921CE 921CE Analyzer Serial Number AE-921-6434 AE-921- 6434AE-921-6434
Operating Range 201 201 201 201.000 Operating Units ppm ppm ppm No. Readings/Avg. 60 60 60 60.000 Calibration Set 312 312 312 312.000 Calibration Pre Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Pre Zero Cylinder Instrument Response 3.443 2.853 2.853 3.050 Calibration Pre Zero Cylinder Bias 2.06 1.76 1.76 1.860 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID ALM045659- SO2-MidALM045659

-SO2-MidALM045659-

SO2-Mid Calibration Pre High Cylinder Instrument Response 95.732 96.027 96.716 96.158 Calibration Pre High Cylinder Bias -3.38 -3.23 -2.89 -3.167 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-SO2 NitrogenSO2Nitrogen-SO2
Calibration Post Zero Cylinder Instrument Response 2.853 2.853 2.262 2.656 Calibration Post Zero Cylinder Bias 1.76 1.76 1.47 1.663 Calibration Post Zero Cylinder Drift 0.3 0 0.29 0.197 Calibration Post High Cylinder ID ALM045659- SO2-MidALM045659

-SO2-MidALM045659-

SO2-Mid Calibration Post High Cylinder Instrument Response 96.027 96.716 97.601 96.781 Calibration Post High Cylinder Bias -3.23 -2.89 -2.45 -2.857 Calibration Post High Cylinder Drift 0.15 0.34 0.44 0.310 Cavg 55.546 56.354 56.831 56.244 Cavg Units ppmvd ppmvd ppmvd Cgas 55.94 56.6369 56.7972 56.458 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 42 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - Method 7E Average Run Number 3-1 3-2 3-3 Test Date 7/9/2010 7/9/2010 7/9/2010 Run Start Time 12:59:00 PM2:42:00 PM 4:12:00 PM Run Finish Time 2:09:00 PM3:42:00 PM 5:11:00 PM Carbon Dioxide, % 5.162 5.198 5.185 5.182 Oxygen, % 13.841 13.918 13.929 13.896 Fuel Factor 1.37 1.34 1.34 Dry Volumetric Flow Rate, dry scfm 194364.8 191824.1 185775190,654.633 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Moisture, % 5.5 5.5 5.5 5.500 Analyzer Make Thermo Electron Thermo

Electron Thermo

Electron Analyzer Model 42 CLS 42CLS 42 CLS Analyzer Serial Number 032820242703282024270328202427328,202,427 .000 Operating Range 201 201 201 201.000 Operating Units ppm ppm ppm No. Readings/Avg. 60 60 60 60.000 Calibration Set 11 11 11 11.000 Calibration Pre Zero Cylinder ID Nitrogen-Nox NitrogenNoxNitrogen-Nox
Calibration Pre Zero Cylinder Instrument Response 0.878 0.488 0.683 0.683 Calibration Pre Zero Cylinder Bias 0.29 0.1 0.19 0.193 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID ALM045659- NOx-MidALM045659

-NOx-MidALM045659-

NOx-Mid Calibration Pre High Cylinder Instrument Response 94.531 95.361 96.191 95.361 Calibration Pre High Cylinder Bias -1.11 -0.7 -0.29 -0.700 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID Nitrogen-Nox NitrogenNoxNitrogen-Nox
Calibration Post Zero Cylinder Instrument Response 0.488 0.683 0.732 0.634 Calibration Post Zero Cylinder Bias 0.1 0.19 0.22 0.170 Calibration Post Zero Cylinder Drift 0.19 0.09 0.03 0.103 Calibration Post High Cylinder ID ALM045659- NOx-MidALM045659

-NOx-MidALM045659-

NOx-Mid Calibration Post High Cylinder Instrument Response 95.361 96.191 96.142 95.898 Calibration Post High Cylinder Bias -0.7 -0.29 -0.31 -0.433 Calibration Post High Cylinder Drift 0.41 0.41 0.02 0.280 Cavg 55.75 55.329 54.794 55.291 Cavg Units ppmvd ppmvd ppmvd Cgas 57.9511 57.0493 56.2061 57.069 Cgas Units ppmvd ppmvd ppmvd Fuel Type Oil Oil Oil Fw 10320 10320 1032010,320.000 Fc 1420 1420 1420 1,420.000 Cgasw 0 0 0 0.000 Cgasw Units



### Tuesday, February 22, 2011 Page 43 of 44

### 2411 PSEG Sewaren Unit 3
9/30/2010
LocationStack Exit - OTM - 27/28 Average Run Number 1 2 3 Test Date 7/6/2010 7/7/2010 7/8/2010 Run Start Time 4:00:00 PM1:00:00 PM 8:30:00 AM Run Finish Time 10:05:00 PM7:08:00 PM 2:17:00 PM Net Traversing Points 12 12 12 Net Run Time, minutes 338.77 347.94 330.31 Nozzle Diameter, inches 0.17 0.171 0.171 0.171 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.9906 0.9906 0.9906 0.991 Barometric Pressure, inches of Mercury 29.855 29.895 29.935 29.895 Average Orifice Meter Differential, inches H2O 0.49 0.49 0.49 0.490 Dry Gas Meter Volume Sampled, cubic feet 134.099 137.887 130.547 134.178 Average Dry Gas Meter Temperature, °F 111.63 105.00 94.88 103.837 Dry Gas Meter Volume Sampled, dscf 122.581 127.693 123.265 124.513 Total Moisture Liquid collected, g 237.4 235.1 241.2 237.900 Volume of Water Vapor, standard cubic feet 11.17 11.07 11.35 11.197 Moisture Content of Stack Gas, % 8.35 7.98 8.43 8.253 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9165 0.9202 0.9157 0.917 Carbon Dioxide, % 8.5 7.3 7.5 7.767 Oxygen, % 9.8 11 10.8 10.533 Carbon Monoxide & Nitrogen, % 81.7 81.7 81.7 81.700 Fuel Factor 1.31 1.36 1.35 Dry Molecular Weight, lb/lb-Mole 29.75 29.61 29.63 29.663 Wet Molecular weight, lb/lb-Mole 28.77 28.68 28.65 28.700 Flue Gas Static Pressure, inches of H2O 0.2 0.2 0.2 0.200 Absolute Flue Gas Pressure, inches of Mercury 29.87 29.91 29.95 29.910 Average Stack Gas Temperature, °F 292.50 267.42 257.25 272.390 Average Velocity Head, inches of H2O 0.8405864811 408680.885105045

7783350.798758400

296064 0.841
Average Stack Gas Velocity, feet/second 61.61 62.21 58.68 60.833 Stack Cross-Sectional Area, square feet 159.812 159.812 159.812 159.812 Dry Volumetric Flow Rate, dry scfm 379,267.3 398,296.6 379,666.7385,743.533 Actual Wet Volumetric Flue Gas Flow Rate, acfm 590,761.0 596,514.3 562,666.1583,313.800 Percent Isokinetic of Sampling Rate, % 96.7 92.3 98.5 95.833 Percent Excess Air, % 83.3 104.1 100.3 95.900 F-Factor, dscfm/MMBtu @ %O2 9190 9190 91909,190.000 Round Duct Diameter, inches 14.263 14.263 14.263 Rectangular Duct Width, inches 151.7 151.7 151.7 Rectangular Duct Length, inches 151.7 151.7 151.7 Fw 10320 10320 1032010,320.000 Fc 1420 1420 14201,420.000



### Tuesday, February 22, 2011 Page 44 of 44