## United States Environmental Protection Agency

General Permit for New or Modified Minor Sources of Air Pollution in
Indian Country

http://www.epa.gov/air/tribal/tribalnsr.html



## General Air Quality Permit for New or Modified True Minor Source Boilers

Last Modified: July 2 , 2014

Version 1.0

Information about this General Permit:

Applicability

P ursuant to the provisions of the Clean Air Act (CAA) , Subchapter I, part D and 40 CFR part 49, subpart C, this permit

authorizes the construction or modification, and operation of each stationary boiler for which a reviewing authority

issues an Approval of the Reques t for Coverage (permitted source)

.

Eligibility

To be eligible for coverage under this general p ermit, the permitted source must qualify as a true minor source as

defined in 40 CFR 49.152.

Request for Coverage

Requirements for submitting a Request for Coverage are contained in Section 7 of this general permit.

Incorporation of D ocuments

The information contained in each reviewing auth ority’s Approval of the Request of Coverage is hereby incorporated

into this general permit

.

Termination

Section 6 of this general permit addresses a reviewing authority’s ability to revise, revoke and reissue, or te rminate this

general permit. It also addr esses the reviewing authority’s ability to terminate an individual permitted source’s Approval

of the Request for Coverage under this general permit.

Definitions

The terms used herein shall have the meaning defined in 40 CFR 49.152 and in Attachment B of this permit. If a term is

not defined, it shall be interpreted in accordance with normal business use.General Permit for Boilers Page 2 of 14

Version 1. 0 Permit Terms and Conditions

The following applies to each p ermittee and permitted source with r espect to only the affected emissions units and any associated air pollution control equipment listed in that permitted source’s Approval of the Request for Coverage.

Section 1

– General Provisions

1. Construction and Operation

The permittee shall construct or modify, an d operate the affected emission units and any associated air pollution

control equipment in compliance with this permit and all other applicable federal air quality regulations; and in a

manner consistent with the Request for Coverage.

2. Location

This permit only authori zes the p ermittee to construct or modify, and operate the permitted source in the location

listed in the reviewing authority’s Approval of the Request for Coverage for that permitted source

.

3. Liability

This permit does not release the p ermittee from any liability for compliance with other applicable federal and tribal

environmental laws and regulations, including the CAA

.

4. Severability

The provisions of this permit are severable. If any portion of this permit is hel d invalid, the remaining terms and

conditions of this permit shall remain valid and in force.

5. Compliance

T he p ermittee must co mply with all provisions of this permit, including emission limitations that apply to the

affected emissions units at the permitted source. Noncompliance with any permit provision is a violation of the

permit and may constitute a violation of the CA A ; and is grounds for an enforc ement action ; and is grounds for the

reviewing authority to revoke the Approval of the Request for Coverage and terminate the permitted source’s

coverage under this general permit.

6. National Ambient Air Quality Standards ( NAAQS ) / Prevention of Significant Deterioration ( PSD ) Protection

T he permitted source must not cause or contribute to a NAAQS violation and , in an attainment area, must not cause

or contribute to a PSD increment violation.

7. Unavailable Defense

It is not a defense for the p ermittee in an enforcement action that it would have been necessary to halt or reduce

the permitted activity in order to maintain compliance with the provisions of this permit.

8. Property Rights

The permit does not convey any property rights of any sort or any exclusive privilege.

9. Information Requests

You, as t he p ermittee

, shall furnish to the reviewing authority, within a reasonable time, any information that the

reviewing authority may request i n writing to determine whether cause exists for revising, revoking and reissuing, or

terminating the permit or to determine compliance with the permit. For any such information claimed to be

confidential, the p ermittee must submit a claim of confidentiali ty in accordance with 40 CFR part 2 subpart B.General Permit for Boilers Page 3 of 14

Version 1. 0 10. Inspection and Entry

Upon presentation of proper credentials, the p ermittee must allow a representative of the reviewing authority to:

a. Enter upon the premises where a source is located or emissions

- related activity is conducted or where records

are required to be kept under the conditions of the permit;

b. Have access to and copy, at reasonable times, any records that are required to be kept under the conditions of

the permit;

c. Inspect, during normal business ho urs or while the source is in operation, any facilities, equipment (including

monitoring and air pollution control equipment), practices or operations regulated or required under the

permit;

d. Sample or monitor, at reasonable times, substances or parameters for the purpose of assuring compliance with

the permit or other applicable requirements ; and

e. Record any inspection by use of written, electronic, magnetic and photographic media.

11. Posting of Coverage

Sections 1 through 6 of this general permit

, and the mo st current Approval of the Request for Coverage for the

permitted source, must be pos ted prominently at the facility, and each affected emissions unit and any

associated air pollution control equipment must be labeled with the identification number listed in the

Approval of the Request for Coverage for that permitted source.

12. Duty to O btain Source

- Specific Permit

If the reviewing authority intends to terminate a permitted source’s coverage under this general permit for cause as

provided in Section 6 of this general permit , then the p ermittee shall apply for and obtain a source

- specific permit

under 40 CFR 49.155 as required by the reviewing authority.

13. Credible Evidence

For the purpose of establishing whether the p ermittee violated or is in violation of any requirement of this permit,

nothing shall preclude the use, including the exclusive use, of any credible evidence or information relevant to

whether a source would hav e been in compliance with applicable requirements if the p ermittee had performed the

appropriate performance or compliance test or procedure

.

14. Setbacks

The exhaust from each boiler or heater must be located a minimum of 50 feet from the nearest property l ine and

150 feet from any adjacent residential or commercial establishment or place of public assembly.

Section 2: Emission Limitations and Standards

15. The permittee shall m aintain and operate each affected emission unit, including any associated air pollution control

equipment, in a manner consistent with good air pollution control practices for minimizing emissions of NSR

regulated pollutants and considering the manufacturer’s recommended operating procedures at all times, including

periods of startu p, shutdown, maintenance and malfunction

. The reviewing authority will determine whether the

p ermittee is using acceptable operat ing and maintenance procedures based on information available to the

reviewing authority which may include, but is not limited to, monitoring results, opacity observations, review of

operating and maintenance procedures, and inspection of the permitted source.

16. The maximum rated capacity of any individual boiler at this facility shall be less than 100 million British thermal units

( MMBtu ) /h ou r (hr)

.General Permit for Boilers Page 4 of 14

Version 1. 0 17. The maximum rated capacity of any individual process heater at this facility shall be:

a. L ess than 10 MMBtu/ hr if located at a permitted source in an ozone attainment, unclassifiable or

attainment /unclassifiable area.

b. Less than 10 MMBtu / hr if located at a permitted source in a marginal, moderate or serious ozone

nonattainment areas.

c. Less than 2 MMBtu/ hr if located at a permitted source in a severe or extreme ozone nonattainment area.

d. A process heater may exceed the above size limitations if it meets the emission limitations applicable to boilers.

18. The combined maximum rated capacity of all boilers and process heaters at the permitted source shall not exceed

the following parameters, as applicable :

a. Each permitted source employing only natural gas boilers and process heaters shall meet the following

combined maximum allowable rating of emission units, based on ozone designation/ attainment area status

. Natural gas

- only boilers and process heaters may also use d iesel or biod iesel as an emergency backup fuel for

up to 500 hour s per calendar year

.

Permitted Source Using Only Natural Gas in Boilers and Heaters

Types of Emission Unit Combined Allowed Maximum Rating of Emissions Units

Ozone Designation/Attainment Area Status

Attainment,

Unclassifiable or
Attainment /

Unclassifiable Nonattainment

Marginal, Moderate,

or Serious Severe

All boilers rated ≥ 10.0 MMBtu/ hr 160 MMBtu/ hr 160 MMBtu/ hr 100 MMBtu/ hr

All small boilers and process heaters rated < 10.0 MMBtu/ hr 20 MMBtu/ hr 20 MMBtu/ hr 20 MMBtu/ hr

All emergency generators (all fuels) 1500 horsepower

( hp ) 1500 hp 1000 hp

b. Each permitted source employing boilers and heaters that use gaseous and/or liquid fuels shall meet the

following combined maximum allowable rating of emission units, based on ozone designation/attainment area

status

.

Permitted Source Using Gaseous and/o r Liquid Fuels in Boilers and Heaters

Types of Emission Units Combined Maximum Rating of Emissions Units

Ozone Designation/Attainment Status

Attainment,

Unclassifiable or
Attainment /

Unclassifiable Nonattainment

Marginal,

Moderate, or

Serious Severe

All boilers rated ≥ 10.0 MMBtu/ hr 120 MMBtu/ hr 120 MMBtu/ hr 100 MMBtu/ hr

All small boilers and auxiliary

heaters rated < 10.0 MMBtu/ hr 20 MMBtu/ hr 20 MMBtu/ hr 20 MMBtu/ hr

All emergency generators (all fuels) 1500 hp 1500 hp 1000 hpGeneral Permit for Boilers Page 5 of 14

Version 1. 0 c. Each permitted source locating in an extreme ozone nonattainment area shall employ only natural gas boilers

and heaters that meet the following combined maximum allowable rating of emission units.

Permitted Sources Locating in Extreme Ozone Nonattainment Areas

(Using Only Natural Gas in Boilers and Heaters)

Types of Emission Units Combined Allowed Maximum

Rating of Emissions Units

All boilers rated ≥ 2.0 MMBtu/ hr 100 MMBtu/ hr

All small boilers and auxiliary

heaters rated < 2.0 MMBtu/ hr 20 MMBtu/ hr

All emergency generators (all fuels) 750

19. For each affected boiler rated at 10.0 MMBtu/ hr or greater, nitrogen oxide ( NO X ) emissions shall not exceed 30.0

parts per million, dry volume ( ppm d v ) at 3% O 2 or 0.037 pounds ( lb s) /MMBtu based on a 15

- minute average.

20. For each affected boiler rated at 10.0 MMBtu/ hr or greater, carbon monoxide ( CO ) emissions shall not exceed 400.0

ppm d v at 3% O 2 or 0.30 lb s /MMBtu based on a 15

- minute average.

21. E ach affected boiler, heater, or engine burning liquid fuels shall use diesel or biodiesel

. The sulfur content of diesel

and biodiesel shall not exceed 0.0015 parts per million ( ppm ) by weight.

22. For e ach affected boiler o r heater, the permittee shall not cause to be discharged into the atmosphere any gases

that exhibit 5 percent opacity or greater averaged over any six consecutive minute period.

23. Each boiler located at a permitted source in an extreme or severe ozone nonat tainment area shall meet the se additional requirements :

a. The NO

x emissions from each boiler rated at 2.0 MMBtu/ hr or greater shall not exceed 9 ppm dv at 3% oxygen or

0.011 lb s /MMBtu based on a 15

- minute average

. b. The CO emissions from each boiler rated at 2.0 MMBtu/ hr or greater shall not exceed 400 ppm dv at 3% O 2 or

0.30 lb s /MMBtu based on a 15

- minute average

.

24. Each boiler stack shall:

a. B e above the buildings in the vicinity,

b. D ischarge vertically, and

c. H ave no obstructions to gas flow such as rain caps, except for hinged rain caps.

25. Each boiler must undergo tune

- ups on a biennial basis . Each biennial tune

- up must be conducted no more than 25

months after the previous tune

- up. The first biennial tune

- up must be no later than 25 months after the Approval of

Request for Coverage is issued . The permittee shall perform each tune

- up as follows:

a. The p ermittee shall inspect the burner and clean or replace any components as necessary. This step may be

delayed until the next scheduled shutdown of the unit, but it must be performed at least once every 36 months.

b. The p ermittee shall inspect the flame pattern and adjust the burner as necessary to optimize the flame pattern.

The adjustment should be consi stent with the manufacturer’s specifications

.

c. The p ermittee shall inspect the system controlling the air

- to

- fuel ratio and ensure that it is correctly calibrated

and functioning properly.

d. The p ermittee shall optimize total emission s of CO . This opt imization should be consistent with the

manufacturer’s specifications.General Permit for Boilers Page 6 of 14

Version 1. 0 e. The p ermittee shall measure the concentrations in the effluent stream of CO in parts per million, by volume, and

oxygen in volume percent, before and after the adjustments are made.

26. If the permitted source includes one or more emergency engines, each affected emergency engine shall:

a. Be equipped with a non

- resettable hour meter;

b. If using fuel oil, use diesel or biodiesel containing no more than 15 ppm (0.0015 percent) sulfur;

c. Meet the following certification requirements for compression ignition emergency engines:

i. For model year 2006 and later engines, the engine shall be certified to the applicable standards in 40

CFR part 89.

d. Meet the following requirements for spark ignition emerge ncy engines manufactured on or after January

1, 2009:

i. Gasoline and rich burn liquified petroleum gas ( LPG ) emergency engines greater than 25 hp and less

than 130 hp shall be certified by the manufacturer to the Phase I standards in 40 CFR 90.103 ;

ii. Gasoline and rich burn LPG emergency engines greater than or equal to 130 hp shall be certified by

the manufacturer to the standards in 40 CFR 1048 ; and

iii. All other spark ignition emergency engines (those that are not gasoline or rich burn LPG) greater than

25 HP shall meet the standards for emergency engines in Table 1 to 40 CFR Subpart JJJJ. If the

emergency engine is not certified to the standards in Tabl e 1 to 40 CFR Subpart JJJJ, then the

permittee shall demonstrate compliance with the applicable emission limitations as required by

Condition 30

.

e. If not required to meet the standards in Conditions 2 6 .c or 2 5

. d based on the engine model year or date

of m anufacture :

i. Follow the manufacturer’s emission

- related operation and maintenance instructions or develop your

own maintenance plan which must provide to the extent practicable for the maintenance and

operation of the engine in a manner consistent with good air pollution control practice for minimizing

emissions;

ii. Change oil and filter and inspect every hose and belt every 500 hours of operation or annually,

whichever comes first; and

iii. Inspect air cleaner or spark plugs, as applicable, every 1,000 hours of ope ration, or annually,

whichever comes first.

Section 3: Monitoring and Testing Requirements

27. Visible Emissions Survey

At least once during each calendar week in which the permitted source s operates

, the p ermittee shall perform a

visible emissions survey of all affected emission units subject to the opacity limit in Condition 2 2 . The survey shall be

performed during daylight hours by an individual trained in EPA Method 22 while the source is in operation. If visibl e emissions are detected during the survey, the p ermittee shall either:

a. Take corrective action so that within 24 hours no visible emissions are detected from any emission units while

they are in operation; or

b. Demonstrate compliance with the opacity limit a t all units that discharged visible emissions during the survey

using EPA Method 9 by an individual trained and certified in Method 9.

28. Initial Performance Testing

Within 60 days after achieving the maximum production rate at which the permitted source wil l operate the

affected emissions unit(s), but not later than 180 days after the first day of operation after the reviewing authority

issues the Approval of the Request for Coverage, the permittee shall perform an initial performance test to verifyGeneral Permit for Boilers Page 7 of 14

Version 1. 0 complian ce with the applicable emission limitations in Conditions 1 9

, 20 and 2 3

. Perfor mance tests shall be

performed:

a. According to an EPA

- approved test plan;

b. While the permitted source is operating under typical operating conditions;

c. Using test methods from 40 CF R part 60, A ppendix A

. In lieu of the test methods from 40 CFR part 60, A ppendix

A, measurements for NO

x and CO may be taken using portable analyzers according to ASTM D6522

- 00, as
incorporated by reference in 40 CFR 63.14(b)(27) ; and

d. Simultaneously for CO and NO

x whenever either one needs to be tested.

29. Additional Performance Testing

Ongoing performance tests meeting the criteria of the initial performance test in Condition 2 8 shall be performed:

a. When required by the reviewing authority; and

b. At least every five years.

30. Emergency Engines Not Certified by the Manufacturer

For each emergency engine required to meet the standards in Condition 2 6 .d .iii , but that is not certified by the

manufacturer to the applicable standards, and is not required to b e certified by the manufacturer, the permittee

shall:

a. For an engine greater than 25 hp and less than or equal to 500 hp, conduct an initial performance test as

follows:

i. W ithin 60 days after achieving the maximum production rate at which the permitted sourc e will operate,

but not later than 180 days after the first day of operation after issuance of the Approval of the Request for

Coverage ;

ii. The test shall verify compliance with the applicable emission limitations in Condition 2 6

. d .iii

. ;

iii. According to a test plan approved by the reviewing authority;

iv. While the permitted source is operating under typical operating conditions;

v. With at least three test runs, each of at least 1 hour duration;

vi. Within 10 percent of peak load for the engine;

vii. Using test methods from 40 CFR part 60, Appendix A unless alternative methods are approved by the

reviewing authority in writing in advance of the test; and

viii. Simultaneously for carbon monoxide and nitrogen oxides whenever either one needs to be tested.

b. For an engine greater than 500 hp , conduct an initial performance test and subsequent performance testing

every 8,760 hours of operation or 3 years, whichever comes first as follows :

i. The performance tests shall verify compliance with the applicable emission limitations in Condition 2 6

. d .iii

. ii. The performance tests shall be performed according to Condition s 30 .a.iii through viii

.

Section 4: Recordkeeping Requirements

31. The permittee shall maintain all records required to be kept by this permit onsite for at least five years from the date

of origin, unless otherwise stated

.

32. T he permit application and all documentation supporting that application shall be maintained by the permittee for

the duration of time the affected emissions unit ( s ) is/ are covered under this permit.

33. T he permittee shall keep records of diesel and biodiesel supplier certifications to demonstrate compliance with the

sulfur content limits in Conditions 21 and 2 6 .b . The certification shall contain the sulfur content of the fuel and th e

method used to determine the sulfur content.General Permit for Boilers Page 8 of 14

Version 1. 0 34. Each natural gas boiler or heater using diesel or biodiesel as an emergency backup fuel shall maintain records on a

quarterly basis of the hours of emergency fuel use.

35. The dates and results of each visible e missions survey pe rformed pursuant to Condition 2 7 shall be recorded

. At a

minimum, records shall include:

a. The name of the person , company or entity conducting the survey;

b. Whether visible emissions were detected from any affected emission unit;

c. Any corrective action taken;

d. The result of any corrective action; and

e. The results of any Method 9 tests performed.

36. The permittee shall record the concentration of CO in the effluent stream in parts per million, by volume, and

oxygen in volume percent, measures before and after the tune

- up of each boiler or heater according to Condition

25

.

37. The permittee shall record any corrective actions taken as part of a tune

- up of a boiler.

38. For each emergency engine, the permittee shall:

a. M aintain a log of all main tenance activities conducted ; and

b. Maintain a log of the hours of operation

, including the date, time, duration, and reason (s) for use

.

39. The results of each performance test conducted pursuant to Condition 28, 29 and 30 shall be recorded. At a

minimum, the permittee shall maintain records of:

a. The date of each test;

b. Each test plan;

c. Any documentation required to approve an alternate test method;

d. Conditions during the test, including the engine power rating;

e. The results of each test; and

f. The name of the compan y or entity conducting the analysis.

Section 5: Notification and Reporting Requirements

40. Notification of C onstruction or M odification, and O perations

T he p ermittee shall submit a written or electro nic notice to the reviewing authority within 30 days from when the

p ermittee begins actual construction or modification , and when the p ermittee begins operations or resumes

operation

.

41. Noti fication of Change in Ownership

If the permitted source changes ownership, then th e p ermittee must submit a written or electronic notice to the

reviewing authority within 90 days after the change in ownership is effective. In the report, the p ermittee must
provide the reviewing authority a written agreement containing a specific date fo r transfer of ownership, and an

effective date on which the new owne r assumes partial and/ or full coverage and liability under this permit. The

submittal must identify the previous owner, and update the name, street address, mailing address, contact

infor mation, and any other information about the source if it would change as a result of the change of ownership.

The p ermittee shall ensure that the permitted source remains in compliance with the general permit during any

such transfer of ownership.General Permit for Boilers Page 9 of 14

Version 1. 0 42. Notification of Closure

The p ermittee must submit a report of any permanent or indefinite closure to the reviewing authority in writing

within 90 days after the cessation of all operations at the permitted source. The notification must identify the

owner, the current location, and the last operating location of the permitted source. It is not necessary to submit a

report of closure for regular, seasonal closures.

43. Annual Reports

The p ermittee shall submit an annual report on or before March 15 of each ye ar to the reviewing authority. The

annual report shall cover the period from January 1 to December 31 of the previous year and shall include:

a. An evaluation of the permitted source’s compliance status with the requirements of Section 2 during the

calendar y ear ;

b. Summaries of the required monitoring , testing and recordkeeping in Sections 3 and 4; and

c. Summaries of deviation reports submitted pursuant to Condition 4 4

.

44. Deviation Reports

The p ermittee shall promptly report to the reviewing authority any deviations from permit requirements including

deviations attributable to upset conditions. Deviation reports shall include:

a. I dentity of the affected emissions unit (s) where the deviation occurred ;

b. N atu re of the deviation;

c. L ength of time of the deviation;

d. P robable cause of the deviation; and

e. Any corrective actions or preventive measures taken as a result of the deviation to minimize emissions from the

deviation and to prevent future deviations.

f. For the purposes of this permit, promptly mean s :

i. Within 7 2 hours of discovery for deviations from any opacity o r emission limit in Condition 18, 19, 2 0 or 22 ;

or

ii. At the time of the annual report required by Condition 4 3 for all other deviations.

45. Performance Test Reports

The p ermittee shall submit a test report to the reviewing authority within 45 days after the completion of any

required performance test. At a minimum, the test report shall include:

a. A description of the emissions unit and samplin g location(s);

b. The time and date of each test;

c. A summary of test results, reported in units consistent with the applicable standard;

d. A description of the test methods and quality assurance procedures used;

e. A summary of any deviations from the proposed test plan and justification for why the deviation(s) was

necessary;

f. The amount and type of fuel burned, raw material consumed, and /or product produced , as applicable, during

each test run;

g. Operating parameters of the source and control equipment during each test run;

h. Sample calculations of equations used to determine test results in the appropriate units ; and

i. The name of the company o r entity performing the analysis

.

46. Rep orting and Notifica tion Address

The p ermittee shall send all required reports to the reviewing authority at the mailing address specified in the

Approval of the Request for Coverage.General Permit for Boilers Page 10 of 14

Version 1. 0 47. Signature Verifying Truth, Accuracy, and Completeness

All reports required by this permit shall be signed by a responsible official as to the truth, accuracy, and

completeness of the information. The report must state that, based on information and belief formed after

reasonable inquiry, the statements and in formation are true, accurate, and complete. If the p ermittee discovers that

any reports or notification submitted to the reviewing authority contain false, inaccurate, or incomplete

information, the p ermittee shall notify the reviewing authority immediately and correct or amend the report as soon

as is practicable.

Section 6 : Changes to this General Permit

48. Revising, Reopening, Revoking and Reissuing, or Terminating for Cause

The permit may be revised, reo pened, revoked and reissued or terminated for cause. The filing of a request by you,

the p ermittee , for a permit revision, revocation and re

- issuance, or termination, or of a notification of planned

changes or anticipated noncompliance does not stay any pe rmit condition. This provision also applies to the

documents incorporated by reference.

49. Terminating Coverage under this Permit

The reviewing authority may terminate a previously issued Approval of the Request for Coverage

, and thereby

terminate that p ermittee ’s authorization to construct or modify, and th at permitted source’s authorization to

operate under this general permit for cause as defined in Attachment B. The reviewing authority may provide the

p ermittee with notice of the intent to terminate, and delay the effective date of the termination to allow the

p ermittee to obtain a case

- by

- case permit under 40 CFR 49.155.

50. Change in O wnership

If the permitted source changes ownership, the reviewing authority ma y change the Approval of the Request of

Coverage to reflect the new ownership in accordance with the administrative amendment provisions in 40 CFR
49.159(f)

.

Section 7 : Obtaining Coverage under this General Permit

51. To obtain coverage under this general permit, an applicant must submit a Request for Coverage to the appropriate

reviewing authority for the area in wh ich the permitted source is or will be located. Attachment C contains a list of

reviewing authorities and their area s of coverage

.

52. You must also submit a copy of the Request for Coverage to the Indian Governing Body for any area within Indian

country in which the permitted source will locate at the same time you submit your Request for Coverage to the

reviewing authority.General Permit for Boilers Page 11 of 14

Version 1. 0 

### Attachment A: Abbreviations and Acronyms

ASTM American Society for Testing and Materials

Btu British thermal unit

CAA Federal Clean Air Act

CFR Code of Federal Regulations

CO carbon monoxide

EPA United States Environmental Protection Agency

hp horsepower

LPG liquified petroleum gas

MM million

NAAQS National A mbient Q ir Q uality S tandards

NO

x nitrogen oxides

, except N 2 O

NSR new source review

ppm parts per million

ppm dv parts per million, dry volume

PSD P revention of S ignificant D eteriorationGeneral Permit for Boilers Page 12 of 14

Version 1. 0 

### Attachment B: Definitions

For the purposes of this general permit:

Approval of the Request for Coverage means a reviewing authorit y’ s letter granting a n applicant’s request for

construction or modification, and operation of a true minor source under the terms and conditions of this general

permit.

Biodiesel means a combustion fuel made from fatty acids of methyl esters that complies with the specifications of ASTM

6751

.

Boiler means an enclosed device using controlled flame combustion in which water is heated to recover thermal energy
in the form of steam and/or hot water. Controlled flame combustion refers to a steady

- state, or near steady

- state, process wherein fuel and/or oxidizer feed rates are controlled. A device combus ting solid waste, as defined in §241.3 of

this chapter, is not a boiler unless the device is exempt from the definition of a solid waste incineration unit as provided

in section 129(g)(1) of the CAA. Process heaters are excluded from the definition of Boil er

.

Cause means with respect to the reviewing authority’s ability to terminate a permitted source’s coverage under a permit

that :

1. The p ermittee is not in compliance with the provisions of this g eneral p ermit;

2. The reviewing authority determines that the emissions resulting from the construction or modification of the

permitted source significantly contribute to NAAQS violations, which are not adequately addressed by the

requirements in this g eneral p ermit.

3. The reviewing authority has reasonable cause to believe that the p ermittee obtained Approval of the Request

for Coverage by fraud or misrepresentation.

4. The p ermittee failed to disclose a material fact required by the Request for Coverage or the regulations

ap plicable to the permitted source of which the applicant had or should have had knowledge at the time the

p ermittee submitted the Request for Coverage.

Construction means any physical change or change in the method of operation including fabrication, erect ion,

installation, demolition, or modification of an emission unit that would result in a change of emissions.

Distillate f

uel means fuel oils, including recycled oils that comply with the specifications for fuel oil numbers 1 and 2, as

defined by ASTM 39 6, or equivalent

.

Natural g as means a mixture of hydrocarbons that is a gas at standard conditions and is either composed of at least 70

percent methane by volume or has a gross calorific value of between 950 and 1150 B tu per dry standard cubic foot

.

Permittee means the owner or operator of a permitted source.

Permitted s ource means each boiler for which a reviewing authority issues an Approval of the Request for Coverage.

Process heater means an enclosed device using controlled flame, and the unit's primary purpose is to transfer heat

indirectly to a process material (liquid, gas, or solid) or to a heat transfer material (e.g., glycol or a mixture of glycol and

water) for use in a process unit, instead of generating steam. Process heaters are devices in which the combustion gases
do not come into direct contact with process materials. Process heaters include units that heat water/water mixtures for

pool heating, sidewalk heating, cooling tower water heating, power washing, or oil heating.General Permit for Boilers Page 13 of 14

Version 1. 0 Request for Coverage means a permit application that contains all the information required in the standard application

form.

Standard c ubic f

oot means a measure of the quantity of a gas equal to a cubic foot of volume at a temperature of 68 °F

and a pressure of 29.92 in ches of mercury.General Permit for Boilers Page 14 of 14

Version 1. 0 

### Attachment C

– List of the EPA Reviewing Authorities and Areas of Coverage

EPA
Region Address Area Covered Phone Number

Region 1 1 Congress Street

Suite 1100

Boston, MA 02114

– 2023 Connecticut, Maine, Massachusetts,

New Hampshire, Rhode Island, and

Vermont 888

- 372

- 7341

617

- 918

- 1111

Region 2 290 Broadway

25th Floor

New York, NY 10007

– 1866 New Jersey, New Yor k, Puerto Rico, and

Virgin Islands 877

- 251

- 4575

Region 3 1650 Arch Street

Philadelphia, PA 19103

– 2187 Delaware, District of Columbia,

Maryland, Pennsylvania, Virginia, and

West Virgin i a 800

- 438

- 2474

215

- 814

- 5000

Region 4 Sam Nunn Atlanta Federal Center

61 Forsyth Street SW

12th Floor

Atlanta, GA 30303 Alabama, Florida, Georgia, Kentucky,

Mississippi, North Carolina , South

Carolina, and Tennessee 800

- 241

- 1754

404

- 562

- 9000

Region 5 77 West Jackson Boulevard

Chicago, IL 60604 Illinois, Indiana, Michigan, Minnesota,

Ohio, and Wisconsin 800

- 621

- 8431

312

- 353

- 2000

Region 6 1445 Ross Avenue

Dallas, TX 75202 Arkansas, Louisiana, New Mexico,

Oklahoma, an d Texas 800

- 887

- 6063

214

- 665

- 2760

Region 7 901 North 5th Street

Kansas City, KS 6 6101

– 2907 Iowa, Kansas, Missouri, and Nebraska 800

- 223

- 0425

913

- 551

- 7003

Region 8 1595 Wynkoop Street

Denver, CO 80202

– 1129 Colorado, Montana, North Dakota,

Sou th Dakota, Utah, and Wyoming 800

- 227

- 8917

303

- 312

- 6312

Region 9 75 Hawthorne Street

San Francisco, CA 94105 American Samoa, Arizona, California,

Guam, Hawaii, Navajo Nation, Nevad a,

and Northern Mariana Islands 866

- 372

- 9378

415

- 947

- 8000

Region 10 1200 Sixth Avenue

Seattle, WA 98101 Alaska , Idaho, Oregon, and Washington 800

- 424

- 4372

206

- 553

- 1200