7

- C

- i APPENDIX 7

- C
. CALCULATION OF FURNA CE BLOWER FAN ENERGY CONSUMPTION
TABLE OF CO NTENTS
7

- C.1 INTRODUCTION

................................ ................................ ................................ . 7

- C

- 1 7

- C.2 SYSTEM CURVES

................................ ................................ ............................... 7

- C

- 1 7

- C.3 FURNACE FAN CURVES

................................ ................................ ................... 7

- C

- 2 7

- C.4 FAN POWER

................................ ................................ ................................ ......... 7

- C

- 8 7

- C.5 DETERMINATION OF FAN CURVES FOR EACH EFFI CIENCY LEVEL AND PRODUCT CLASS

................................ ................................ .................... 7

- C

- 12
LIST OF TABLES
Table 7

- C.3.1 Coefficients for CFM equation for PSC motors

................................ .. 7

- C

- 3 Table 7

- C.3.2 Coefficients for CFM equation for Two

- Stage and Continuous Modulating furnaces with ECM motors

................................ .............. 7

- C

- 6 Table 7

- C.4.1 Coefficients for W/CFM equation for PSC motors

............................. 7

- C

- 9 Table 7

- C.4.2 Coefficients for W/CFM equation for Two

- Stage and Continuous Modulating furnaces with ECM motors

................................ ............ 7

- C

- 11 Table 7

- C.5.1 Coefficients for CFM equation for Non

- Weatherized (Non

Condensing) Gas Fur nace Fan, 3

- Ton

................................ ............... 7

- C

- 13 Table 7

- C.5.2 Coefficients for Watts/CFM Equation for Non

- Weatherized (Non

Condensing) Gas Furnaces, 3

- Ton

................................ ..................... 7

- C

- 16
LIST OF FIGURES Figure 7

- C.2.1 Sample of System Curves with a Typical Fan Curve

.......................... 7

- C

- 2 Figure 7

- C.3.2 Example Fit of CFM for 3

- ton Single

- Stage (High Fire) Furnace

....... 7

- C

- 4 Figure 7

- C.3.3 Fan Curves for Single

- Stage Virtual Model Furnaces

......................... 7

- C

- 5 Figure 7

- C.3.4 Fan Curves for Two

- Stage Virtual Model Furnaces

– High Fire

........ 7

- C

- 7 Figure 7

- C.3.5 Fan Curves for Two

- Stage Virtual Model Furnaces

– Low Fire

......... 7

- C

- 7 Figure 7

- C.4.1 Example Fit of Watts/CFM for 3

- ton Single

- Stage Furnace

............... 7

- C

- 9 Figure 7

- C .4.2 Watts/CFM vs. Pressure Curves for Single

- Stage Virtual Model Furnaces

................................ ................................ ............................. 7

- C

- 10 Figure 7

- C.4.3 Watts/CFM vs. Pressure Curves for Two

- Stage Virtual Model Furnaces

– High Fire

................................ ................................ .......... 7

- C

- 11 Figure 7

- C.4.4 Watts/CFM vs. Pressure Curves for Two

- Stage Virtual Model Furnace s

– Low Fire

................................ ................................ .......... 7

- C

- 12 Figure 7

- C.5.2 CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Heating Mode)

................................ ............................... 7

- C

- 14 Figure 7

- C.5.3 CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Cooling Mode)

................................ ............................... 7

- C

- 157

- C

- ii Figure 7

- C.5.4 CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Continuous Fan Mode)

................................ .................. 7

- C

- 1 6 Figure 7

- C.5.5 Watt/CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Heating Mode)

................................ ................. 7

- C

- 17 Figure 7

- C.5.6 Watt/CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Cooling Mode)

................................ ................. 7

- C

- 18 Figure 7

- C.5.7 Watt/CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Continuous Fan Mode)

................................ .... 7

- C

- 19 Figure 7

- C.5.8 Resulting Watt vs. Pressure Curves for Non

- Weatherized (Non

Condensing) Gas Furnace Fan, 3

- Ton (Heating Mode)

..................... 7

- C

- 20 Figure 7

- C.5.9 Resulting Watt vs. Pressure Curves for Non

- Weatherized (Non

Condensing) Gas Furnace Fan, 3

- Ton (Cooling Mode)

.................... 7

- C

- 21 Figure 7

- C.5.10 Resulting Watt vs. Pressure Curves for Non

- Weatherized (Non

Condensing) Gas Furnace Fan, 3

- Ton (Continuous Fan Mode)

........ 7

- C

- 227

- C

- 1 APPENDIX 7

- C. CALCULATION OF FURNA CE BLOWER FAN ENERGY CONSUMPTION
7

- C.1 I NTRODUCTION The electricity consumption (and overall efficiency) of a blower motor depends on the speed at which the motor operates, the external static pressure difference across the blower, and the airflow through the blower. To calculate blower

- motor electricity consumption, DOE determined the op erating conditions (the pressure and airflow) at which a particular furnace in a particular housing unit will operate. These operating conditions can be graphically displayed as the intersection of a system curve of the ducts in the housing unit (which pl ots the airflow across the supply and return air ducts as a function of static pressure) with the fan curve of the furnace (which plots the airflow through the furnace as a function of static pressure). The intersection of these two curves is the airflow and the static pressure at which the furnace will operate in that housing unit. Furnace fan curves, reported as tables of airflow rise versus static pressure through the furnace, are available from manufacturers in the product literature for each furnace . Some of the manufacturers also supply blower

- motor input power as a function of static pressure across the furnace. Air power is calculated from the air speed through the furnace and the pressure rise across the furnace. The overall air

- moving effici ency is air power divided by the electric power to the blower motor. All the electric power of the blower motor eventually is converted to heat that contributes to meet ing the building heating load.

7

- C.2 SYSTEM CURVES The system curve of the air

- distributio n system is a graphical representation of the airflow through the supply and return ducts in a house for different static pressure. The airflow and pressure drop at which the furnace will operate can be determined by the intersection of the system curve o f the house and the fan curve of the furnace circulating air blower. 1
The Department modeled system curves as quadratic curves, which is standard in heating, ventilation, and air conditioning (HVAC) design and fan selection handbooks. 2 The curves are based on Bernoulli’s equations for fluid flow and are expressed as the following equation:

Q = � P
α
where:7

- C

- 2 Q = airflow (cfm), P = static pressure (in.w.g.), and
α = a constant coefficient. The Department selected the coefficient in the system curve equation for each housing unit. It randomly sampled a coefficient from one of four distributions, depending on the nominal maximum airflow of the virtual model furnace selected for that housing u nit. The Department designed each distribution so that 10 percent of samples would have static pressures below 0.5 in.w.g., and 1 percent of the samples would have static pressures greater than 1 in.w.g at the nominal maximum airflow. This is in line wit h several field studies. 3 To keep the system curves from clumping at the h igher pressures, the Department used a log

- normal distribution of values of the coefficient. See Figure 7

- C.2.1 for an example of a plot of system curves intersect ing a furnace fan curve.

0 400 800 1200 1600

0.00 0.25 0.50 0.75 1.00 External Static Pressure (in. w.g.) Airflow (CFM)

Highest 1%
median
Lowest 10% 1200 CFM Generic Single-Stage Furnace Model (Heating Tap)

Figure 7

- C.2.1 Sample of System Curves with a Typical Fan Curve

7

- C.3 FURNACE FAN CURVES Depending on the resistance (measured as static pressure) of the supply and return air ducts, a furnace will move more or less air. When these airflow values are plotted graphically against pressure, they are referred to as fan curves.7

- C

- 3 The Department developed fan curves for the single

- stage (High Fire modes) virtual furnace models and for two

- stage (High Fire and Low Fire modes) by fitting the manufacturer airflow and pressure data points from the basic model furnaces 4, 5, 6, 7, 8, 9, 10 to a second

- order polynomial. The Department did this separately for each of the four nominal air handler sizes. The CFM for PSC blower motors is given by the following equation:

CFM = m 0 + m 1 × ( P ) + m 2 × ( P 2 ) Eq. 1 where,
CFM = airflow in CFM reported by manufacturer,
m 0,1,2, and 3 = coefficients derived from 2 n d degree polynom ial approximation (see Table 7

- C.3.1 for actual coefficient values), and P = external static pressure (in

. w.g.).

Table 7

- C.3.1 Coefficients for CFM equation for PSC motors High Fire (Single

- Stage) Low Fire
m 0 m 1 m 2 m 0 m 1 m 2 2

- ton 840.8

- 42.5

- 494.9 712.8

- 87.7

- 400.4 3

- ton 1158.0

- 12.1

- 507.2 930.6 99.1

- 527.3 4

- ton 1522.7

- 40.3

- 527.0 1158.6 36.1

- 463.6 5

- ton 1877.5

- 102.8

- 485.0 1469.0 37.8

- 453.2
Figure 7

- C.3.2 shows an example of a CFM curve for a 3

- ton Non

- Condensing Single

Stage Furnace fitted with the manufacturers’ raw data.7

- C

- 4 Figure 7

- C.3.2 Example Fit of CFM for 3

- ton Single

- Stage (High Fire) Furnace Figure 7

- C.3.3 show s the fan curves for PSC furnaces. Appendix 7

- G contains the data on the basic models that were used to develop these fan curves. 0 500 1000 1500 2000 2500

0.00 0.10 0.20 0.30 0.40 0.50 0.60 0.70 0.80 0.90 1.00 Pressure (in.w.g.) Air Flow (CFM) L1RA072*12B L1RA090*12B M1BB-086-*** M1GB-090-*** M1GH-077-*** M1GH-090-*** M1MB-056-*** M1MB-090-*** RGPN-10(E,N)AMER GUIC070**30 TUD060C936K* TUE060A936L* RGPN-07(E,N)AMER G40DF-36A-070-* G50DF-36A-070-* TDD060C936F* TDE060A936M* DPGB075A3* MPGA075B3* RGPJ-07EAUER M1BB-086-*** M1GB-090-*** M1GH-077-*** M1GH-090-*** M1MB-056-*** M1MB-090-*** P4HUA12N03201 P4HUA12N04801 P4HUA12N06401 ABA080NH3R N8MPL050B12 N8MPN050B12 P4DNA12N03201 P4DNA12N04801 P4DNA12N06401 T8MPL050B12 T8MPN050B12 58DLA045-12 58DLX045-12* 58STA045-12 58STX045-12* G40DF-36C-110-** G50DF-36C-110-** 58DLA070-12 58DLX070-12* 58STA070-12 58STX070-12* RGLJ-07EAUER G40DF-36B-090-*7

- C

- 5 Figure 7

- C.3.3 Fan Curves for Single

- Stage Virtual Model Furnaces
The two

- stage and continuous modulating design options in this analysis use brushless permanent magnet motors (or sometimes referred as Electronically Commutated Motors (ECM)). Unlike PSC motors, these motors are electronically commutated and the speed they operate at can be varied across a wide range. These motors are controlled to operate the blower fans at a wide variety of air flows and static pressures. In furnaces with these motors currently on the market, the controls are designed to provide a near constant air flow across the entire range of pressures at which they operate. Because of the versatility of the motors, manufacturers only offer furnaces with blowers nominally designed for operation with five

- ton and three

- ton air conditioners. The manufacturers provide control options to decrease the airflow for installations that use smaller air conditioners. To develop fan curves for furnaces with ECM motors, the Department fit quadratic curves through th e air flow and pressure data points reported by manufacturers. 11, 12, 13, 14, 15, 16, 17 DOE did this separately for high

- fire and low

- fire operation. See Figure 7

- C.3.4 through Figure 7

- C.3.5 for charts showing the fit li nes. Table 7

- C.3.2 shows the coefficients for two

- stage and continuous modulating furnaces with ECM motors below . Data from the basic models that were used to develop these fan curves is shown in Appendix 7

- H , Determination of Basic Furnace Models. 0 500 1000 1500 2000 2500

0.00 0.25 0.50 0.75 1.00 External Static Pressure (in. w.g.) Airflow (CFM) 2000 CFM 1600 CFM 1200 CFM 800 CFM7

- C

- 6 CFM = m 0 + m 1 × ( P ) + m 2 × ( P 2 ) where,
CFM = airflow in CFM reported by manufacturer,
m 0,1, and 2 = coefficients derived from 2 nd degre e polynomial approximation (see Table 7

- C.3.2 for actual coefficient values), and P = external static pressure (in.w.g.).

Table 7

- C.3.2 Coefficients for CFM equation for Two

- Stage and Continuous Modulating furnaces with ECM motors High Fire Low Fire
m 0 m 1 m 2 m 0 m 1 m 2 2

- ton 785.1 46.9

- 135.1 580.7 17.5

- 81.5 3

- ton 1043.2 23.5

- 101.1 779.3 2.6

- 64.0 4

- ton 1326.2 57.6

- 61.9 946.7 6.5 13.8 5

- ton 1571.9 5.6

- 30.5 1160.9

- 17.7 1.1
To be consistent with the analysis it did for the single

- stage furnaces with PSC blower motors, the Department created virtual models for furnaces intended to act as air handlers for four and two ton air conditioners , even though these are not currently offered by manufacturers. To generate the fan curve s for the virtual furnaces intended to be used with 4 ton air conditioners, DOE calculated the average of the slopes and intercepts of the virtual furnaces with air handler for 5 ton and 3 ton air conditioners. This was done separately for high and low fi re operations for non

- condensing and condensing furnaces. For the virtual furnace models intended to operate with two

- ton air conditioners, the fan curves were created by extrapolating the values for the slopes and intercepts of the virtual furnace model s with air handlers intended to operate with three

- ton and five

- ton air conditioners. This was also done separately for high fire and low fire operation for both non

condensing and condensing furnaces. See Figure 7

- C.3.4 through Figure 7

- C.3.5 for charts showing the fan curves for these air handlers.7

- C

- 7 Figure 7

- C.3.4 Fan Curves for Two

- Stage Virtual Model Furnaces

– High Fire

Figure 7

- C.3.5 Fan Curves for Two

- Stage Virtual Model Furnaces

– Low Fire 0 500 1000 1500 2000 2500

0.00 0.25 0.50 0.75 1.00 External Static Pressure (in. w.g.) Airflow (CFM) 2000 CFM 1600 CFM 1200 CFM 800 CFM

0 500 1000 1500 2000 2500

0.00 0.25 0.50 0.75 1.00 External Static Pressure (in. w.g.) Airflow (CFM) 2000 CFM 1600 CFM 1200 CFM 800 CFM7

- C

- 8 7

- C.4 FAN POWER Once the operating point of air flow and static pressure is determined by finding the intersection of the fan curve and the system curve, the watts per cubic feet per minute (CFM) of airflow are determined using the equations developed in this appendix. The power consumption of the fan at this operating condition, BE, is calculated by multiplying the Watts/CFM by the CFM at the operating po int:

BE = � Watts CFM � × Q
where,

BE = circulating air fan electrical energy consumption (watts), Watts/CFM = determined below , and Q = airflow (cfm). For furnaces with air handlers with permanent split capac it o r (PSC) blower motors, one manufacturer reports watts across a range of pressures. For these models, the Department divided watts at these pressures by air flow in CFM at these same pressures. These values of watts per CFM across a range of pressures were fit to a second order pol ynomial for the basic furnace models made by the manufacturer. The Department did this separately for each of the four nominal air handler sizes. The watts per CFM for PSC blower motors is given by the following equation:

Watts CFM = m 0 + m 1 × ( P ) + m 2 × ( P 2 )
where,
Watts/CFM = blower electricity consumption in watts reported by manufacturer divided by the airflow in CFM at the same static pressure,
m 0,1, and 2 = coefficients derived from 2 nd degree polynomial approximation (see Table 7

- C.4.1 for actual coefficient values), and P = external static pressure (in.w.g.).7

- C

- 9 Table 7

- C.4.1 Coefficients for W/CFM equation for PSC motors High Fire (Single

- Stag e) Low Fire
m 0 m 1 m 2 m 0 m 1 m 2 2

- ton 0.395

- 0.161 0.258 0.384

- 0.140 0.332 3

- ton 0.432

- 0.209 0.185 0.425

- 0.204 0.209 4

- ton 0.416

- 0.191 0.156 0.428

- 0.195 0.152 5

- ton 0.449

- 0.124 0.096 0.449

- 0.130 0.086
Figure 7

- C.4.1 shows the Watts per CFM curve for 3

- ton condensing single

- stage furnace fitted to the manufacturers’ data. A similar process of fitting curves to data was done for each nominal air handler size.

Figure 7

- C.4.1 Example Fit of Watts/CFM for 3

- ton Single

- Stage Furnace Figure 7

- C.4.2 show s the fit curves of Watts/CFM for pressures from 0 in.w.g. to 1.0 in.w.g. Data from the models that were used to develop these fan curves is shown in Appendix H, Determination of Basic F urnace and Boiler Models. 0 0.1 0.2 0.3 0.4 0.5 0.6

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1 Pressure (in.w.g.) Watt/CFM G51MP-36B-045-**
G43UF-36B-070-**
G51MP-36B-070-**
G43UF-36C-090-**
G43UF-36C-090H-**
G51MP-36C-090-**
data fit7

- C

- 10 Figure 7

- C.4.2 Watts/CFM vs. Pressure Curves for Single

- Stage Virtual Model Furnaces
For the two

- stage and continuous modulating furnaces with ECM motors, the Department calculated watts per CFM equations using data from basic models of se veral manufacturers. These data are in the reduced set of furnace models database. This was done for basic model furnaces nominally designed for use with 3 ton and 5 ton air conditioners. The watts per CFM data points of these basic models were fit to straight lines using Equation 4 . To be consistent with other analyses, the Department calculated the slope and intercept for the watts per CFM curves for furnaces intended to operate with 2 ton and 4 ton air conditioners by interpolating from the value s for 3 ton and 5 ton air handlers. Figure 7

- C.4.3 through Figure 7

- C.4.4 show the lines for the basic models. Table 7

- C.4.2 shows the coefficients for two

- stage and continuous modulating furnaces with ECM motors using Eq. 3. Data fr om the models used to develop these fan curves is shown in Appendix H, Determination of Basic Furnace and Boiler Models.

Watts CFM = m 0 + m 1 × ( P ) + m 2 × ( P 2 ) Eq. 4 where,
Watts/CFM = blower electricity consumption in watts reported by manufacturer divided by the airflow in CFM at the same static pressure, 0.0 0.2 0.4 0.6

0.00 0.25 0.50 0.75 1.00 External Static Pressure (in. w.g.) Watts/CFM

2000 CFM 1600 CFM 1200 CFM 800 CFM7

- C

- 1 1 m 0,1 , and 2 = coefficients derived from second degree polynomial (see Table F

C .4. 2 for actual coefficient values), and P = external static pressure (in. w.g.).

Table 7

- C.4.2 Coefficients for W/CFM equation for Two

- Stage and Continuous Modulating furnaces with ECM motors High Fire Low Fire
m 0 m 1 m 2 m 0 m 1 m 2 2

- ton 0.143 0.247

- 0.048 0.090 0.239 0.005 3

- ton 0.160 0.239

- 0.029 0.100 0.240 0.003 4

- ton 0.170 0.311

- 0.084 0.104 0.251 0.012 5

- ton 0.190 0.264

- 0.029 0.117 0.246 0.004

Figure 7

- C.4.3 Watts/CFM vs. Pressure Curves for Two

- Stage Virtual Model Furnaces

– High Fire 0.0 0.2 0.4 0.6

0.00 0.25 0.50 0.75 1.00 External Static Pressure (in. w.g.) Watts/CFM 2000 CFM 1600 CFM 1200 CFM 800 CFM7

- C

- 12 Figure 7

- C.4.4 Watts/CFM vs. Pre ssure Curves for Two

- Stage Virtual Model Furnaces

– Low Fire
7

- C.5 DETERMINATION OF FAN CURVES FOR EACH EFFI CIENCY LEVEL AND PRODUCT CLASS In order to generate the fan performance data used in the analysis DOE applied the following procedure (the 3

- ton baseline PSC motor for non

- weatherized (non

- condensing) gas furnaces is used as an example):
STEP 1: Using the coefficients to generate for airflow (cfm) vs. pressure and watts/cfm vs. pressure curves at each airflow speed (heating, cooling, and continuous fan), DOE found the airflow cfm and watts per CFM at DOE’s reference system curve external static pressure. For example, DOE’s reference system curve external static pressure is 0.65 in. w.g at the maximum cooling airflow speed for non

- weatherized gas furnaces. For the 3

- ton baseline PSC motor for non

- weatherized (non

- condensing) gas furnaces the maximum airflow CFM was calculate to be 1158 cubic feet per minute.
STEP 2: Using the BE equation above, DOE multiplied the airflow times the watt/cfm at each pressure from Step 1 to calculate BE at each airflow speed (heating, cooling, and continuous fan) in terms of DO E’s reference system curve external static pressure. For example, for the 3

- ton baseline PSC motor for non

- weatherized (non

- condensing) 0.0 0.2 0.4 0.6

0.00 0.25 0.50 0.75 1.00 External Static Pressure (in. w.g.) Watts/CFM 2000 CFM 1600 CFM 1200 CFM 800 CFM7

- C

- 13 gas furnaces BE was calculate to be 382 watts at heating, 495 watts at cooling, and 382 watts at continuous fan.
STEP 3: Using the calculated maximum airflow CFM and BE values at DOE’s reference system curve external static pressure, DOE was able to calculate Furnace Efficiency Rating (FER) values. For example, for the 3

- ton baseline PSC motor for non

weatherized (non

- con densing) gas furnaces FER was calculate d as 363.
STEP 4: The constant curve fit parameter ( m 0 ) in the pressure and watts/cfm vs. pressure
curves was then adjusted using an adjustment multiplier in order to match the FER values derived in the engineering a nalysis. For example, for the 3

- ton baseline PSC motor for non

- weatherized (non

- condensing) gas furnaces the FER value derived in the engineering analysis was 380, so the adjustment multiplier to convert the FER value calculated in step 3 was calculate d as 1.04.
Table 7

- C.5.1 shows the airflow (cfm) vs. pressure coefficients determined for non

weatherized (non

- condensing) gas furnaces (3

- ton) at each efficiency lev el (EL). Figure 7

- C.5.2 to Figure 7

- C.5.4 show the resulting curves at various pressures and operating modes.

Table 7

- C.5.1 Coefficients for CFM equation for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton E L Heating Cooling Continuous Fan
m 0 m 1 m 2 m 0 m 1 m 2 m 0 m 1 m 2 0 1158

- 12

- 507 1523

- 280

- 432 1158

- 12

- 507 1 1158

- 12

- 507 1523

- 280

- 432 931 99

- 527 2 1059 269

- 405 1277 198

- 516 667

- 117

- 44 3 1139

- 403

- 62 1427

- 323

- 15 1001

- 880 214
4 1043 24

- 101 1203 8

- 26 679 3

- 64
5 1043 24

- 101 1203 8

- 26 679 3

- 647

- C

- 14 Figure 7

- C.5.2 CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Heating Mode) 600 700 800 900 1000 1100 1200

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Airflow (CFM)

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 15 Figure 7

- C.5.3 CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Cooling Mode) 600 700 800 900 1000 1100 1200 1300 1400 1500 1600

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Airflow (CFM)

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 16 Figure 7

- C.5.4 CFM Curves for Non

- Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Continuous Fan Mode)
Table 7

- C.5.2 shows the watts/cfm vs. pressure curves coefficients determined for non

weatherized (non

- condensing) gas furnaces (3

- ton) at each efficiency level. Figure 7

- C.5.5 to Figure 7

- C.5.7 show the resulting curves at various pressures

. Figure 7

- C .5.8 to Figure 7

- C.5.10 show the resulting Watts vs. pressure curves.

Table 7

- C.5.2 Coefficients for Watts/CFM Equation for Non

- Weatherized (Non

Condensing) Gas Furnaces, 3

- Ton E L Heating Cooling Continuous Fan
m 0 m 1 m 2 m 0 m 1 m 2 m 0 m 1 m 2 0 0.45

- 0.21 0.19 0.46

- 0.12 0.15 0.45

- 0.21 0.19 1 0.45

- 0.21 0.19 0.46

- 0.12 0.15 0.44

- 0.20 0.21 2 0.30 0.16 0.02 0.35 0.16

- 0.03 0.22 0.15 0.14 3 0.15 0.10 0.10 0.24 0.12 0.04 0.13 0.01 0.42
4 0.12 0.24

- 0.03 0.13 0.29

- 0.04 0.07 0.24 0.00
5 0.09 0.24

- 0.03 0.10 0.29

- 0.04 0.06 0.24 0.00 0 200 400 600 800 1000 1200 1400

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Airflow (CFM)

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 17 Figure 7

- C.5.5 Watt/ CFM Curves for Non

- Weatherized (Non

Condensing) Gas Furnace Fan, 3

- Ton (Heating Mode) 0.00 0.10 0.20 0.30 0.40 0.50 0.60

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Watts/CFM

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 18 Figure 7

- C.5.6 Watt/ CFM Curves for Non

- Weatherized (Non

Condensing) Gas Furnace Fan, 3

- Ton (Cooling Mode) 0.00 0.10 0.20 0.30 0.40 0.50 0.60

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Watss/CFM

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 19 Figure 7

- C.5.7 Watt/ CFM Curves for Non

- Weatherized (Non

Condensing) Gas Furnace Fan, 3

- Ton (Continuous Fan Mode) 0.00 0.10 0.20 0.30 0.40 0.50 0.60

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Watts/CFM

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 20 Figure 7

- C.5.8 Resulting Watt vs. Pressure Curv es for Non

Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Heating Mode) 0 100 200 300 400 500 600

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Watts

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 21 Figure 7

- C.5.9 Resulting Watt vs. Pressure Curves for Non

Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Cooling Mode) 0 100 200 300 400 500 600 700 800

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Watss

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 22 Figure 7

- C.5.10 Resulting Watt vs. Pressure Curves for Non

Weatherized (Non

- Condensing) Gas Furnace Fan, 3

- Ton (Continuous Fan Mode) 0 100 200 300 400 500 600

0 0.1 0.2 0.3 0.4 0.5 0.6 0.7 0.8 0.9 1Watts

External Static Pressure (in w.c.) Baseline (PSC) Improved PSC PSC w/ Controls X13 ECM (Variable Speed) ECM + BC Impeller7

- C

- 23 REFERENCES
1. Michael R. Lindeburg, P., Fans and Ductwork . In Mechanical Engineering Reference Manual for the PE Exam , P. Michael R. Lindeburg, Editor. Tenth ed. 1997. Professional Publications, Inc.: Belmont, CA. p. 20

- 1, 20

- 26
2. American Society of Heating Refrigeration and Air

- Conditioning Engineers, ASHRAE 1997 Handbook

- Fundamentals . 1997. Atlanta, GA.p. 3.12.
3. Proctor, J. and D. Parker, Hidden Power Drains: R esidential Heating and Cooling Fan Power Demand. In ACEEE 2000 Summer Study on Energy Efficiency in Buildings. 2000. Asilomar, CA, August 20

- 25. American Council for an Energy

- Efficient Economy.1: pp. 225

- 234.
4. Lennox Industries Inc., Lennox Engineerin g Data: G50DF (Elite Series Downflow Gas Furnace), 2003. Lennox Industries, Inc. < http://pirl.lennox.com/C03e7o14l/76E0ZC21u/ehb_g50df_0307.pdf >
5. Lennox Industries Inc., Lennox Engineering Data: G50UH (Elite Series Upflow/Horizontal Gas Furnace), 2003. Lennox Industries, Inc. < http://pirl.lennox.com/C03e7o14l/76E0ZC21u/ehb_g50uh_0307.pdf >
6. Lennox Ind ustries Inc., Lennox Engineering Data: G40DF (Merit Series Upflow/Horizontal Gas Furnace), 2003. Lennox Industries, Inc. 2003.) < http://pirl.lennox.com/C03e7o14l/76E0ZC21u/ehb_g40d f_0307.pdf >
7. Lennox Industries Inc., Lennox Engineering Data: G43UF (Merit Series Upflow Gas Furnace), 2004. Lennox Industries, Inc. < http://pirl.lennox.com/C03e7o14l/76E0ZC21u /ehb_g43uf_0412.pdf >
8. Lennox Industries Inc., Lennox Engineering Data: G41UF (Merit Series Downflow Gas Furnace), 2004. Lennox Industries, Inc. < http://pirl.lennox.com/C03e7o14 l/76E0ZC21u/ehb_g41uf_0402.pdf >
9. Lennox Industries Inc., Lennox Engineering Data: G51MP (Elite Series Multi

- Position Gas Furnace), 2004. Lennox Industries, Inc. < http://pirl.lennox.com/C03e7o14l/76E0ZC21u/ehb_g51mp_0412.pdf >
10. Lennox Industries Inc., Lennox Engineering Data: G40UH (Merit Series Upflow/Horizontal Gas Furnace), 2004. Lennox Industries, Inc. < http://pirl.lennox.com/C03e7o14l/76E0ZC21u/ehb_g40uh_0407.pdf >7

- C

- 24 11. Carrier Co., 58MVP, Deluxe 4

- Way Multipoise Variable

- Capacity Direct

- Vent Condensing Gas Furnace, 2004. Carrier Co. Catalog No. 535

- 80141, Form 58MVP

– 12SM.
12. Carr ier Co., 58CVA/CVX, InfinityTM 80, Variable Speed, 4

- Way Multipoise Furnace, 2004. Carrier Co. Form 58CV

- 3PD. Catalog No. 525

- 80043.
13. Lennox Industries Inc., Lennox Engineering Data: G60DFV (Down

- flow

- Variable Speed Blower

- Two

- Stage Heat) . 2004, Le nnox Industries, Inc.
14. Lennox Industries Inc., Lennox Engineering Data: G60UHV (Up

- Flow/Horizontal

- Two Stage Heat

- Variable Speed Blower) . 2003, Lennox Industries, Inc.
15. Lennox Industries Inc., Lennox Engineering Data: G61MPV (Multi

- Position

- Variable Speed Blower

- Two

- Stage Heat

- Direct Vent/Non

- Direct Vent) . 2004, Lennox Industries, Inc.
16. Trane Co., Trane Product Data: XV 80, 2004. Trane Co.
17. Trane Co., Trane Product Data: XV 90, 2004. Trane Co.