EMISSIONS TEST REPORT 

POLK POWER STATION 

UNIT 1 

FACILITY ID NUMBER: 1050233 

EMISSION UNIT ID NO: -001 

SULFURIC ACID MIST (SAM) 

February 7, 2006 

Prepared For: 

Tampa Electric Company 

Polk Power Station 

P.O. Box 111 

Tampa, Florida 33601-0111 

Prepared By: 

Tampa Electric Company 

Environmental Affairs Department 

Environmental Services, Air Services Group 

Environmental Services 

Air Services Group 

5010 Causeway Boulevard

Tampa, Florida 33619- 6130 
REPORT CERTIFICATION 

I have reviewed the test performance, associated quality assurance 

activities, the resultant calculations, and the contents of this report, and certify 

that all project quality objectives have been met. This report is approved for 

submittal. 

Signature:__________________________ 

Raymond A. McDarby, Jr. 

Senior Environmental Technician 

Quality Assurance/Quality Control Specialist

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

The sampling and subsequent data entry/reduction detailed in this report

were conducted at my direction, and I hereby certify that this test report is 

authentic and accurate to the best of my knowledge. 

Signature:__________________________ 

Charles R. Dufeny 

Environmental Technician 

Test Team Lead 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

I have reviewed the testing details and results submitted in this report, 

and hereby certify that this test report is authentic and accurate to the best of 

my knowledge. 

Signature:__________________________ 

David A. Smith 

Coordinator – Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 
TABLE OF CONTENTS

SECTION PAGE NO.

1.0 INTRODUCTION 1 

2.0 DISCUSSION OF RESULTS 2 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES 3 

4.0 TABULATED RESULTS 

SULFURIC ACID MIST TEST SUMMARY 5 

NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 6 

HEAT INPUT CALCULATIONS 7 

5.0 STACK SAMPLING LOCATION DIAGRAM 9 

APPENDICES

A. SULFURIC ACID MIST TEST INFORMATION

CALCULATED RUN DATA 

LABORATORY ANALYSIS 

FIELD DATA SHEETS 

EQUIPMENT CALIBRATIONS 

B. TURBINE DATA (PLANT INFORMATION SYSTEM)

C. FUEL ANALYSIS

D. CEMS DATA

E. VISIBLE EMISSION DATA SHEET

F. TEST PARTICIPANTS
1 

1.0 INTRODUCTION

On February 7, 2006, Tampa Electric Company’s, Environmental Services, Air Services 

Group performed Sulfuric Acid Mist (SAM) source emission tests on Unit No. 1 at the 

Polk Power Station. Unit No. 1 is an integrated coal gasification combined cycle (IGCC) 

generating unit. The combustion turbine was fired with syngas from the coal 

gasification system. A blend of petroleum coke and bituminous coal was gasified for 

this test. Testing was conducted according to United States Environmental Protection 

Agency (USEPA) test methods stipulated in 40 CFR Part 60, Appendix A and Florida 

Department of Environmental Protection (FDEP) Permit No. 1050233-016-AV. 

Nitrogen Oxides (NOx) and Sulfur Dioxide (SO2) data was taken from the Continuous 

Emissions Monitoring System’s (CEMS) Data Acquisition and Handling System (DAHS) 

and is presented as averages over the test period. 
2 

2.0 DISCUSSION OF RESULTS

The Sulfuric Acid Mist (H2SO4) emission rate was derived from three 1-hour test runs. 

The calculated average H2SO4 emission rate was 31 lbs/hr. The FDEP permitted 

emission rate is 55 lbs/hr based on a 30-day rolling average. 

Sulfur Dioxide (SO2) concentration and emissions during the sulfuric acid mist testing 

were determined to be 0.19 lb/mmBtu and 339 lbs/hr. 

Nitrogen Oxides (NOx) concentration and emissions during the sulfuric acid mist testing 

were determined to be 12 ppmvd @ 15% O2 , 0.056 lbs/mmBtu, and 99 lbs/hr. 

During the tests on February 7, 2006, Unit No. 1 Combustion Turbine was operated at 

an average load of 192 megawatts and an average heat input of 1774 mmBtu/hr. The 

FDEP permitted heat input is 1755 mmBtu/hr, at an ambient temperature of 59o 

(corrected to 1751 mmBtu/hr based on an average inlet vane temperature of 73oF, and 

the manufacturer’s heat input correction curve for this unit). The calculated capacity 

factor during the test was 101%. 
3 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generating Station is located at County Road 630 approximately 

13 miles southwest of Bartow, Polk County, Florida. Unit No. 1 is an IGCC generating 

unit, with a net capacity of 192 MW when fired with Syngas fuel. The source sampling 

location consists of a circular stack 19 feet in diameter with four sample ports located 90 

degrees apart on the stack circumference. A diagram of the stack sampling location is 

included along with other pertinent information on the test site. 

Sulfuric acid mist sampling and analysis was performed in accordance with USEPA 

Reference Method 8 (40 CFR Part 60, Appendix A) "Determination of Sulfuric Acid Mist 

and Sulfur Dioxide Emissions from Stationary Sources”, and FDEP Permit No. 1050233-

016-AV, Condition A.56. 

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. 

This data was taken as 1-minute averages over the time frame from 9:12 through 13:49, 

representing the time frame of the sulfuric acid mist test. 

Plant operational data was taken from the Plant Information (PI) server system. This 

data was taken as 1-minute averages over the time period from 9:12 through 13:49, 

representing time frame of the sulfuric acid mist test. Data captured included the 

average unit load, average fuel flow, average inlet vane temperature, and average 

saturator readings. Details are included in Appendix B. 
4 

4.0 TABULATED RESULTS
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Summary

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Test Date: February 7, 2006

Run #1 Run #2 Run #3 Average

Gas Flow Rates

Qs, acfm: 1413087.9 1396668.7 1405512.1 1405089.59

Qs(std), dscfm: 907742.9 902994.6 902109.2 904282.22

Sampled Volume, Vm(std), dscf: 39.69 39.29 39.29 39.421

Stack Moisture, Bws x 100, %: 4.63 4.15 4.49 4.426

Isokinetic Sampling Rate, I, %: 97.6 97.1 97.2 97.3

C H2SO4, lb/dscf: 6.255E-07 5.493E-07 5.092E-07 5.613E-07

E H2SO4, lb/mmBtu: 0.0166 0.0144 0.0137 0.0149

E H2SO4, lbs/hr: 34 30 28 31

5 
7 

POLK POWER STATION

NO X & SO 2 COMPLIANCE DATA FROM CEMS

NOx SO2 O2 CO2 NOx

1 NOx2 SO23 SO24

ppmvw ppmvw % w % w ppmvd @ 15% O2 lbs/hr lb/mmBtu lbs/hr

From CEMS Report: 17.62 43.47 10.46 8.72 12 99 0.19 339

1 NOx, ppmvd @ 15% O2 is calculated as:

NOx, ppmvw / (1 - % moisture) x (5.9 / (20.9 - (% O2w/ (1 - % moisture)))

where: % moisture = 0.07 assumed by CEMS

2

 NOx, lbs/hr is calculated as:

NOx, ppmvw x 1.194E-07 x Fc x (100 / % CO2w) x Heat Input, mmBtu/hr

where: Fc = 2310 scf/mmBtu, assigned F-factor for synthetic gas

Heat Input = 1774 mmBtu/hr

NOx, lbs/mmBtu is calculated as:

NOx, ppmvw x 1.194E-07 x Fc x (100 / % CO2w) 

= 0.056 lbs/mmBtu

3

 SO2, lb/mmBtu is calculated as:

SO2, ppmvw x 1.660E-07 x Fc x (100 / % CO2w)

where: Fc = 2310 scf/mmBtu, assigned F-factor for synthetic gas

4

 SO2, lbs/hr is calculated as:

SO2, lb/mmbtu x Heat Input, mmBtu/hr

where: Heat Input = 1774 mmBtu/hr

CEMS Data are average of readings from 02/07/2006 09:11 through 13:49.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

February 7, 2006

CEM Data Calculated Data
POLK POWER STATION

HEAT INPUT CALCULATION

Average fuel flow: 7306.5726 Kcfh

Mole weight correction to meter cal: 0.9883 mole weight correction factor

Corrected fuel flow:1 7221.0857 Kcfh, corrected for density

Average moisture: 6.2828935 % H20 added to fuel

Corrected fuel flow:2 6767.3926 Kscfh, corrected for moisture

Gross heating value of fuel (HHV): 262.08 Btu/scf

Heat Input: 1774 mmBtu/hr

Average fuel flow from Plant Information Data Base.

Mole weight correction factor to meter calibration is taken from ratio of syngas mole weight

to calibration gas mole weight.

1Average fuel flow times mole weight correction factor.

2Corrected fuel flow times (1 - (Average moisture / 100)).

Gross Heating value of fuel (HHV) is from fuel analysis.

Heat input is (HHV x Corrected fuel flow) / 1000.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

February 7, 2006

7 
8 

5.0 SAMPLING LOCATION TRAVERSE DIAGRAM
9 

UNFIRED HEAT

RECOVERY

BOILER

TRANSITION

DUCT

EXHAUST FROM

TURBINE

14 FT.

38 FT.

150 FT.

136 FT.

 PORT LOCATION PLAN

19.0 FT.ID.

STACK DIAMETERS DOWNSTREAM

FROM DISTURBANCE = 2.0

STACK DIAMETERS UPSTREAM

FROM DISTURBANCE = 0.7

STACK DIAMETER = 19.0 FT.

STACK AREA = 283.529 SQ. FT.

STACK AREA =40828.138 SQ. IN.

 TRAVERSE

 POINTS

 1 - 4.79 ”

 2 - 15.28 ”

 3 - 26.90 ”

 4 - 40.36 ”

 5 - 57.00 ”

 6 - 80.17 ”

 

 ADD 13” PORT LENGTH

 TO POINTS

Polk Power Station

Unit No. 1

IGCC

Test Location
APPENDIX A 

SULFURIC ACID MIST TEST INFORMATION 
CALCULATED RUN DATA 
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 1

Date: 02/07/06

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 29.85 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 29.78 "Hg Average Orifice Meter, ∆H: 1.445 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 39.682 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 71.8 o

F

Gas Analysis: 8.7 % CO2 Average Stack Temp., Ts: 320.3 o

F

10.6 % O2 Average √∆p: 1.223 "H2O

0.0 % CO Condensate Volume, Vlc: 40.9 ml

80.7 % N2 Meter Box Y: 1.006 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 1.928 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (∆H / 13.6)) / (Tm +460) 39.686 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.046 %

FDA = 1.0 - Bws 0.954 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.82 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.27 lb./lb. mole

vs = 85.49 x Cp x (√∆p) x (√(Ts + 460) / (Ms x Ps)) 83.07 ft/second

Qs = vs x As x 60 1413087.9 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 907742.9 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60 97.6 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.00969

Volume Titrant Blank, Vtb 0.01

Volume Titrant Sample, Vt 4.75

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 6.255E-07 lb/dscf

Fc-factor = 2310 dscf/mmBtu

E H2SO4 = C H2SO4 x Fc-factor x (100/%CO2) = 0.01661 lb/mmBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 34 lb/hr
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 2

Date: 02/07/06

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 29.90 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 29.83 "Hg Average Orifice Meter, ∆H: 1.420 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 39.304 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 72.9 o

F

Gas Analysis: 8.8 % CO2 Average Stack Temp., Ts: 320.5 o

F

10.5 % O2 Average √∆p: 1.211 "H2O

0.0 % CO Condensate Volume, Vlc: 36.1 ml

80.7 % N2 Meter Box Y: 1.006 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 1.702 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (∆H / 13.6)) / (Tm +460) 39.285 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.042 %

FDA = 1.0 - Bws 0.958 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.83 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.34 lb./lb. mole

vs = 85.49 x Cp x (√∆p) x (√(Ts + 460) / (Ms x Ps)) 82.10 ft/second

Qs = vs x As x 60 1396668.7 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 902994.6 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x 97.1 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.00969

Volume Titrant Blank, Vtb 0.01

Volume Titrant Sample, Vt 4.13

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 5.493E-07 lb/dscf

Fc-factor = 2310 dscf/MMBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 30 lb/hr
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 3

Date: 02/07/06

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 29.86 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 29.79 "Hg Average Orifice Meter, ∆H: 1.442 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 39.733 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 78.0 o

F

Gas Analysis: 8.6 % CO2 Average Stack Temp., Ts: 322.4 o

F

11.8 % O2 Average √∆p: 1.216 "H2O

0.0 % CO Condensate Volume, Vlc: 39.2 ml

79.6 % N2 Meter Box Y: 1.006 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 1.848 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (∆H / 13.6)) / (Tm +460) 39.292 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.045 %

FDA = 1.0 - Bws 0.955 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.85 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.32 lb./lb. mole

vs = 85.49 x Cp x (√∆p) x (√(Ts + 460) / (Ms x Ps)) 82.62 ft/second

Qs = vs x As x 60 1405512.1 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 902109.2 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x 97.2 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.00969

Volume Titrant Blank, Vtb 0.01

Volume Titrant Sample, Vt 3.83

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 5.092E-07 lb/dscf

Fc-factor = 2310 dscf/MMBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 28 lb/hr
LABORATORY ANALYSIS 
Laboratory Services

5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272

Report For:

Laboratory ID: AA82175

Date and Time Collected:

Sampled By:

Sample Information

Description:

Location Code:

Report Date: 2/13/2006

Polk No. 1 Acid Mist Comp on Syngas

TE_PPS_1_SAM_SYNGAS

Project Account Code:

Sample Collection Method: Date of Sample Receipt: 2/8/2006

Laboratory Results

2/8/2006 12:00:00 AM

PARAMETER Result

Qualifier

Code

Test

Method Analyst Units

Upper

MDL Limit

Violation

Check

Analysis

Date & Time

Lower

Limit

Normality of BaCl2 * 2H2O 0.0001 MM 0.00969 2/8/2006 8:30:00 AM

SO3 emission rate, lbs/hr lbs/hr EPA - RM8 RAM 31 2/13/2006 1:25:00 PM

SO3, Avg. of Blank Titrations milliliters 0.01 EPA - Meth.8 MM 0.01 I 2/8/2006 8:30:00 AM

SO3, Run #1, Avg. of Titrations milliliters 0.01 EPA - Meth.8 MM 4.75 2/8/2006 8:30:00 AM

SO3, Run #2, Avg. of Titrations milliliters 0.01 EPA - Meth.8 MM 4.13 2/8/2006 8:30:00 AM

SO3, Run #3, Avg. of Titrations milliliters 0.01 EPA - Meth.8 MM 3.83 2/8/2006 8:30:00 AM

SO3, Volume of Contained Sample milliliters 1 EPA - Meth.8 MM 500 2/8/2006 8:30:00 AM

SO3, Volume of Sample Aliquot milliliters 0.1 EPA - Meth.8 MM 100 2/8/2006 8:30:00 AM

Comments

Data Qualifier Codes Explanation:

Robert Dorey,

Manager, Laboratory Services

I - The reported value is between the laboratory method detection limit (MDL) and the laboratory practical quantitation limit (PQL). PQL = 4 x MDL.

Subcontracted Laboratories:

All results calculated on a wet to wet basis, unless otherwise indicated.

Report Number: -021306- 13 AA82175 Page 1 of 1

Laboratory Services certifies that the test results in this report meet all requirements of the NELAC standards, unless indicated otherwise in the body of the report.



FIELD DATA SHEETS 






EQUIPMENT CALIBRATIONS 
Environmental Services

Air Services Group

SUMMARY OF EQUIPMENT CALIBRATIONS

EQUIPMENT CAL DATE METHOD RESULTS

CONSOLE (MB 06) USEPA RM 5

INITIAL 01/04/2006 (ORIFICE) 1.006

POST TEST 02/09/2006 1.011

NOZZLE (SN06) CALIPER 

INITIAL 01/04/2006 MEASUREMENTS 0.197

POST TEST 02/09/2006 0.197

PYROMETER (PY 10) 01/04/2006 ASTM THERMOMETER + 2o

 F

PITOT TUBE (PT 10) 10/17/2005 USEPA RM 2 Cp = 0.84

BAROMETER (BR 02) 01/03/2006 NWS COMPARISON + 0.01" Hg
Environmental Services

Air Services Group

Red Team

Manufacturer: Thermo Anderson Calibration Date:

Model Number:MST-C1 Barometric Pressure: 30 "Hg

Instrument Code Number: ^MB06 Theoretical Critical Vacuum: 14.15 "Hg

LabWorks Sample Number: Calibrated By:

Initial Final Total

∆H Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

0.64 15 46.100 52.925 6.825 77 77 77 77

1.15 15 52.925 62.029 9.104 78 77 77 78

1.95 15 62.029 73.770 11.741 77 78 83 78

3.70 15 73.770 89.845 16.075 83 78 89 79

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

48 0.3483 22.5 75 75 75.0

55 0.4660 20.0 75 75 75.0

63 0.5971 19.0 75 75 75.0

73 0.8177 16.0 75 75 75.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ∆Hα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

6.736 6.776 6.851 1.006 0.000 1.739 -0.032

8.989 9.066 9.165 1.009 0.003 1.744 -0.027

11.583 11.617 11.744 1.003 -0.003 1.796 0.025

15.830 15.909 16.083 1.005 -0.001 1.806 0.035

Averages: 1.006 1.771

Review/Approval: Date: 18-Jan-06

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

Quarterly Calibration

1/4/2006

JAV

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.

IMPORTANT

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ∆Hα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice Readings

Ambient Temperatures

CALCULATED DATA

Critical Orifice
Environmental Services

Air Services Group

Manufacturer: Thermo Calibration Date:

Model Number:MST Barometric Pressure: 30.24 "Hg

Instrument Code Number: MB06 Theoretical Critical Vacuum: 14.26 "Hg

LabWorks Sample Number: Calibrated By:

Associated Test: Team: RED

Initial Final Total

∆H Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

1.15 10 978.800 984.870 6.070 80 75 80 76

1.15 10 984.870 990.952 6.082 80 76 80 77

1.15 10 990.952 997.042 6.090 80 77 80 77

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

55 0.4660 21.0 73 72 72.5

55 0.4660 21.0 72 72 72.0

55 0.4660 21.0 72 72 72.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ∆Hα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

6.038 6.107 6.096 1.011 0.001 1.721 0.002

6.044 6.110 6.093 1.011 0.000 1.718 -0.001

6.050 6.110 6.093 1.010 -0.001 1.717 -0.002

Averages: 1.011 1.719

Prior Y: 1.006

% Difference: -0.47%

Review/Approval: Date:

IMPORTANT

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.

Ambient Temperatures

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

Critical Orifice Readings

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

RAB

2/9/2006

POST - TEST CALIBRATION CHECK

2/10/2006

CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ∆Hα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice
Environmental Services

Air Services Group

QUARTERLY NOZZLE CALIBRATIONS

Shared Resource

STEEL NOZZLE SET

Calibration Date: 1/4/2005 Responsible Party: R.A. Barthelette Jr.

Nozzle Nozzle Diameter, Dn (cm) Maximum Average

I.D. D1 D2 D3 Difference, " Dn, inches

^SN01 0.300 0.300 0.300 0.000 0.118

^SN04 0.320 0.320 0.320 0.000 0.126

^SN05 0.380 0.380 0.375 0.002 0.149

^SN06 0.500 0.500 0.500 0.000 0.197

^SN09 0.700 0.700 0.700 0.000 0.276

^SN10 0.755 0.755 0.750 0.002 0.297

^SN12 0.985 0.990 0.990 0.002 0.389

^SN15 0.420 0.420 0.415 0.002 0.165

^SN16 0.500 0.500 0.500 0.000 0.197

^SN19 0.715 0.710 0.710 0.002 0.280

^SN22 0.930 0.935 0.935 0.002 0.367

^SN30 0.795 0.800 0.795 0.002 0.314

^SN36 0.480 0.480 0.480 0.000 0.189

^SN37 0.520 0.525 0.525 0.002 0.206

^SN38 0.640 0.640 0.635 0.002 0.251

^SN46 0.480 0.480 0.480 0.000 0.189

^SN47 0.515 0.515 0.515 0.000 0.203

^SN48 0.640 0.640 0.635 0.002 0.251

^SN50 0.795 0.795 0.790 0.002 0.312

^SN58 0.615 0.615 0.620 0.002 0.243

^SN68 0.630 0.630 0.625 0.002 0.247

^SN69 0.950 0.950 0.955 0.002 0.375

^SN70 1.560 1.560 1.560 0.000 0.614

^SN71 1.560 1.560 1.560 0.000 0.614

^SN72 0.955 0.955 0.955 0.000 0.376

^SN73 1.280 1.285 1.280 0.002 0.505

^SN74 1.245 1.245 1.245 0.000 0.490

Data Notations: All micometer readings are converted from cm to inches by multiplying by

0.393700787. Maximum Difference must be < 0.004".

QA/QC Review by:

Date: 18-Jan-06
Environmental Services

Air Services Group

POST TEST NOZZLE CALIBRATION 

Shared Resource

Calibration Date: 2/9/2006

Calibration Personnel: RAB

Test Designation: Polk 1 SAM Compliance

Nozzle Nozzle Diameter, Dn (cm) Maximum Average

Identifier D1 D2 D3 Difference, " Dn, inches

SN06 0.500 0.500 0.500 0.000 0.197

Data Notations: All micometer readings are converted from cm to inches by multiplying by

0.393700787. Maximum Difference must be < 0.004".

Quarterly (pre-test) value for nozzle ID SN06 was 0.197

Difference (Pre-test/Post-test) is: 0.000

QA/QC Review by: 2/10/06
Environmental Services

Air Services Group

Pyrometer Calibration

Red Team

Pyrometer Under Test

Pyrometer Number: ^PY10

Labworks Sample # N/A

Calibration Date: 1/4/2006

Calibrator Information

Calibrator Type/Manufacturer: Hart Scientific

Calibrator Serial Number: AOA024

Date of Last Calibration: 10/6/2005

Calibration Personnel (Typed and Signature): Jorge A Varino

Calibration Data

Calibration Reference Pyrometer

Point Temperature Indication Difference

1 400 400 0

2 212 211 1

3 32 32 0

Reference temperatures must encompass the expected range of measurement. These three points

should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit.

Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration

Point Difference

1 Pass

2 Pass

3 Pass

Reviewer: Date: 18-Jan-06
Environmental Services

Air Services Group

_ _

s

PITOT TUBE CALIBRATION

DATA SHEET

Pitot Tube ID # PT10

Calibration Date 10/17/2005 Operating Quarter/Year: 4 Shared Resource

Openings Damaged? ___ Y __ N Repaired? ___ Y ___ N ___ N/A

Labworks #: AA79435

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 0.8 degrees Pass Dt 0.48 < Dt > 0.95 cm

α 2 1.2 degrees Pass α < 10 degrees

β 1 0.1 degrees Pass (α1 measured across top impact openings)

β 2 0.2 degrees Pass (α2 measured across bottom impact openings)

β1 < 5 degrees (alongside top impact openings)

Gamma, Theta, Α, Ζ, and W Determination β2 < 5 degrees (alongside bottom impact openings)

ψ 0.1 degrees Ζ < 0.32 cm (Αsinψ)

Α 2.43 cm W < 0.08 cm (Asinο)

Ζ 0.004 cm Pass Α distance between tips

ο angle of plane on side of pitots

ο 1.3 degrees ψ angle between tips

W 0.055 cm Pass

NOTES

All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, 

Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement

details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems:

Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.

Comments: REMOVABLE

Calibrated by: Juan Ramirez

Quality Assurance Review / Approval: 17-Oct-05
Environmental Services

Air Services Group

BAROMETER CALIBRATION

Blue Team

Instrument Number: ^BR02

Calibration Date: 01/03/2006

Calibration Personnel: R.A. Barthelette Jr.

Labworks #:

Barometer Reading Reference Reading Difference

Time Inches Mercury Inches Mercury "Hg

10:35 30.00 30.02 -0.02

12:10 29.98 30.02 -0.04

Average Difference: -0.03

Note: Barometric readings must agree within + 0.1 "Hg.

Current Reference is National Weather Service, TIA.

Current Conditions at Tampa International Airport

Comments (Note any adjustments):

QA/QC Review by: Date: 18-Jan-06
APPENDIX B 

TURBINE DATA 
PI Ops Data

Plant Information Source: polk-1pisrv

Start Time: 2/7/2006 9:12

End Time: 2/7/2006 13:49

Time Interval: 1 Min

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 191.518322 7306.57258 73.4711102 6.28289354

07-Feb-06 09:12:00 192.1288147 7252.82861 64.2213974 6.50704861

07-Feb-06 09:13:00 192.0754547 7251.17871 64.7196884 6.50666714

07-Feb-06 09:14:00 191.7931824 7249.52832 64.9516296 6.50628567

07-Feb-06 09:15:00 191.3609161 7277.23877 65.1835709 6.5059042

07-Feb-06 09:16:00 191.6625671 7322.8335 65.4155121 6.50552273

07-Feb-06 09:17:00 192.0321808 7292.20752 65.20224 6.50514126

07-Feb-06 09:18:00 192.1638336 7258.32861 65.0494995 6.50475979

07-Feb-06 09:19:00 191.526474 7263.60889 65.0697174 6.50437784

07-Feb-06 09:20:00 191.8067017 7273.20752 65.5274124 6.50399637

07-Feb-06 09:21:00 191.6235809 7267.4043 65.8332596 6.5036149

07-Feb-06 09:22:00 191.8021851 7264.8208 65.683548 6.50323343

07-Feb-06 09:23:00 191.8202057 7263.25098 65.6654358 6.50285196

07-Feb-06 09:24:00 191.7798309 7267.70166 66.1231384 6.50247049

07-Feb-06 09:25:00 192.409317 7261.15625 66.2096939 6.50208902

07-Feb-06 09:26:00 192.202179 7261.25586 66.3649597 6.50170755

07-Feb-06 09:27:00 191.5558319 7264.84961 66.8280182 6.50132608

07-Feb-06 09:28:00 192.04216 7259.37988 66.9820099 6.50094461

07-Feb-06 09:29:00 191.9876862 7253.91016 67.1104431 6.50056314

07-Feb-06 09:30:00 191.178421 7257.10059 66.9577026 6.50018167

07-Feb-06 09:31:00 191.2994537 7255.1416 66.7947769 6.49980021

07-Feb-06 09:32:00 191.8082733 7265.95898 66.3365479 6.49941874

07-Feb-06 09:33:00 192.0485687 7287.66943 65.8783264 6.49903727

07-Feb-06 09:34:00 191.6096954 7307.08496 66.7943954 6.4986558

07-Feb-06 09:35:00 191.1708374 7322.44873 67.0119553 6.49827433

07-Feb-06 09:36:00 191.0958099 7366.84131 67.2172775 6.49789286

07-Feb-06 09:37:00 192.1004333 7356.95361 67.4226074 6.49751139

07-Feb-06 09:38:00 192.5331268 7318.75781 67.2643356 6.49712992

07-Feb-06 09:39:00 191.458786 7317.12549 67.4183273 6.49674845

07-Feb-06 09:40:00 191.9042511 7320.34961 67.3008194 6.49636698

07-Feb-06 09:41:00 191.6746216 7312.83252 67.1474533 6.49598551

07-Feb-06 09:42:00 191.5156708 7297.19043 66.9940872 6.49560404

07-Feb-06 09:43:00 192.3639679 7279.85352 66.8407211 6.49522257

07-Feb-06 09:44:00 191.1596069 7279.57959 66.9322433 6.4948411

07-Feb-06 09:45:00 191.4785767 7279.30566 67.0849838 6.49445963

Page 1 of 8
PI Ops Data

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

07-Feb-06 09:46:00 191.7975464 7279.03174 66.8921814 6.49407816

07-Feb-06 09:47:00 191.2572021 7278.72217 67.2617645 6.49369669

07-Feb-06 09:48:00 192.2488708 7278.35547 67.4362946 6.49331522

07-Feb-06 09:49:00 191.8756714 7277.98877 68.0781937 6.49293375

07-Feb-06 09:50:00 191.845871 7265.46973 67.899559 6.49255228

07-Feb-06 09:51:00 191.7506866 7253.87451 68.1305466 6.49217081

07-Feb-06 09:52:00 191.5950623 7257.79102 68.3615341 6.49178934

07-Feb-06 09:53:00 191.7074585 7259.3252 68.5925293 6.49140787

07-Feb-06 09:54:00 191.5588837 7269.65332 69.0480881 6.4910264

07-Feb-06 09:55:00 191.4754791 7268.08252 69.086586 6.49064493

07-Feb-06 09:56:00 191.5470581 7307.62891 69.2405777 6.49026299

07-Feb-06 09:57:00 191.7560425 7302.99023 69.2354507 6.48988152

07-Feb-06 09:58:00 191.9650269 7277.59766 69.0814514 6.48950005

07-Feb-06 09:59:00 191.6876678 7285.26465 69.2948151 6.48911858

07-Feb-06 10:00:00 191.7206726 7275.18066 69.6826248 6.48873711

07-Feb-06 10:01:00 191.9111786 7272.55713 69.8037109 6.48835564

07-Feb-06 10:02:00 191.7337494 7278.2251 69.9247971 6.48797417

07-Feb-06 10:03:00 192.0595093 7277.48535 70.0458832 6.4875927

07-Feb-06 10:04:00 192.0592651 7273.79639 70.1669693 6.48721123

07-Feb-06 10:05:00 191.7153625 7265.36279 69.8368835 6.48682976

07-Feb-06 10:06:00 191.9688568 7256.9292 69.7047348 6.48644829

07-Feb-06 10:07:00 191.6097412 7252.78271 69.9345245 6.48606682

07-Feb-06 10:08:00 191.7392578 7255.5332 70.1643143 6.48568535

07-Feb-06 10:09:00 191.8681488 7252.44971 70.3941116 6.48530388

07-Feb-06 10:10:00 191.996521 7247.854 70.4729385 6.48492241

07-Feb-06 10:11:00 192.1248932 7248.75244 70.3996658 6.48454094

07-Feb-06 10:12:00 192.1385651 7245.2168 71.1160431 6.48415947

07-Feb-06 10:13:00 192.0296021 7253.10059 70.902565 6.483778

07-Feb-06 10:14:00 191.4155579 7251.1875 71.0339432 6.48339653

07-Feb-06 10:15:00 191.5024567 7265.42627 71.1653214 6.48301506

07-Feb-06 10:16:00 191.2958221 7311.85205 71.2966995 6.48263359

07-Feb-06 10:17:00 191.5341339 7304.51855 71.4280853 6.48225212

07-Feb-06 10:18:00 191.9154663 7282.88818 71.5594635 6.48187065

07-Feb-06 10:19:00 191.7777557 7281.91064 71.6908417 6.48148918

07-Feb-06 10:20:00 192.0355835 7280.93262 71.5049973 6.48110771

07-Feb-06 10:21:00 191.7624207 7276.39404 71.6076584 6.48072624

07-Feb-06 10:22:00 192.0516052 7271.88965 71.7103195 6.48034477

07-Feb-06 10:23:00 191.4102325 7276.65674 71.806221 6.4799633

07-Feb-06 10:24:00 191.4327393 7272.84912 71.5032043 6.47958183

07-Feb-06 10:25:00 192.0529938 7267.33691 71.8010025 6.47920036

Page 2 of 8
PI Ops Data

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

07-Feb-06 10:26:00 192.1385345 7281.27051 71.6611786 6.47881889

07-Feb-06 10:27:00 191.7378082 7283.95996 71.5059204 6.47843742

07-Feb-06 10:28:00 191.4309845 7278.11768 71.523819 6.47805595

07-Feb-06 10:29:00 191.59375 7284.27783 71.1850357 6.47767448

07-Feb-06 10:30:00 191.7565155 7285.01074 71.2759399 6.47729301

07-Feb-06 10:31:00 191.919281 7281.80811 71.3595581 6.47691154

07-Feb-06 10:32:00 192.2622223 7280.21631 71.5648804 6.47653008

07-Feb-06 10:33:00 192.3158722 7291.40039 71.7702103 6.47614813

07-Feb-06 10:34:00 191.4996796 7289.72266 71.5648804 6.47576666

07-Feb-06 10:35:00 192.4039459 7297.85645 71.7394104 6.47538519

07-Feb-06 10:36:00 191.2481995 7404.49316 71.6941681 6.47500372

07-Feb-06 10:37:00 192.3108521 7348.31201 71.5414276 6.47462225

07-Feb-06 10:38:00 191.3013458 7349.7417 71.6737061 6.47424078

07-Feb-06 10:39:00 190.992157 7434.78955 71.918663 6.4740715

07-Feb-06 10:40:00 191.3721161 7500.07666 72.16362 6.47623158

07-Feb-06 10:41:00 192.4888611 7421.54688 72.408577 6.47839165

07-Feb-06 10:42:00 192.2049561 7318.70654 72.2843781 6.4805522

07-Feb-06 10:43:00 191.4058075 7304.4082 71.9464417 6.48271227

07-Feb-06 10:44:00 192.1710968 7297.07471 71.9122391 6.48487234

07-Feb-06 10:45:00 192.083725 7318.31152 72.080513 6.48703289

07-Feb-06 10:46:00 191.8710785 7309.0376 72.2487869 6.48919296

07-Feb-06 10:47:00 191.9635773 7296.75342 72.4170609 6.49135303

07-Feb-06 10:48:00 191.8784637 7327.17773 72.4033661 6.49351358

07-Feb-06 10:49:00 192.2067566 7310.27734 72.2194214 6.49567366

07-Feb-06 10:50:00 192.3373413 7326.04248 72.4983978 6.49783373

07-Feb-06 10:51:00 191.1014099 7379.39453 72.7770081 6.49999428

07-Feb-06 10:52:00 192.0639496 7402.92285 72.700325 6.50215435

07-Feb-06 10:53:00 192.5269318 7402.92529 72.623642 6.50431442

07-Feb-06 10:54:00 192.1761169 7320.42822 72.5469666 6.50647497

07-Feb-06 10:55:00 191.6178589 7332.61816 72.3612595 6.50863504

07-Feb-06 10:56:00 191.782135 7390.04053 72.2142105 6.51079559

07-Feb-06 10:57:00 191.8125458 7350.43896 72.4591675 6.51295567

07-Feb-06 10:58:00 192.0511932 7313.7793 72.7041245 6.51511574

07-Feb-06 10:59:00 191.723999 7303.59717 72.9490814 6.51727629

07-Feb-06 11:00:00 192.0197296 7295.82227 73.1246338 6.51943636

07-Feb-06 11:01:00 191.6981659 7312.7998 73.1246338 6.52159643

07-Feb-06 11:02:00 191.5386047 7310.8335 73.1246338 6.52375698

07-Feb-06 11:03:00 191.5522308 7308.86719 73.1246338 6.52579355

07-Feb-06 11:04:00 191.965744 7308.97266 73.1246338 6.5261035

07-Feb-06 11:05:00 191.6070862 7325.55322 73.1246338 6.52641392

Page 3 of 8
PI Ops Data

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

07-Feb-06 11:06:00 191.908905 7318.21973 73.1246338 6.52672386

07-Feb-06 11:07:00 192.0616455 7311.66553 73.1246338 6.52703381

07-Feb-06 11:08:00 191.9385681 7313.68213 73.4377594 6.52734375

07-Feb-06 11:09:00 191.8154907 7315.04199 73.4377594 6.52765369

07-Feb-06 11:10:00 191.9438019 7313.03809 73.7457657 6.52796364

07-Feb-06 11:11:00 191.7696228 7353.52686 73.6690826 6.52827358

07-Feb-06 11:12:00 191.7493134 7386.33008 73.5923996 6.528584

07-Feb-06 11:13:00 192.5530243 7349.96533 73.5157166 6.52889395

07-Feb-06 11:14:00 192.4085236 7316.25781 73.4390411 6.52920389

07-Feb-06 11:15:00 192.0245972 7319.30029 73.5134735 6.52951384

07-Feb-06 11:16:00 191.179657 7381.8999 73.5904694 6.52982378

07-Feb-06 11:17:00 191.7066498 7355.49902 73.6674652 6.53013372

07-Feb-06 11:18:00 192.1019287 7330.39697 73.7444611 6.53044367

07-Feb-06 11:19:00 191.8305054 7321.19189 74.0013733 6.53075361

07-Feb-06 11:20:00 191.4325256 7326.46484 74.022934 6.53106403

07-Feb-06 11:21:00 191.9137726 7330.71533 73.801384 6.53137398

07-Feb-06 11:22:00 191.7647095 7323.71924 74.0162354 6.53168392

07-Feb-06 11:23:00 192.1398621 7316.72314 73.7508774 6.53199387

07-Feb-06 11:24:00 192.4851074 7309.72705 74.1882095 6.53230381

07-Feb-06 11:25:00 191.9763031 7303.63232 74.343483 6.53261375

07-Feb-06 11:26:00 192.2644806 7305.64893 74.2574692 6.5329237

07-Feb-06 11:27:00 191.7315063 7306.49023 74.1047287 6.53323364

07-Feb-06 11:28:00 192.0646973 7298.65088 74.0921707 6.53354406

07-Feb-06 11:29:00 191.7025757 7308.4541 74.1305923 6.53385401

07-Feb-06 11:30:00 192.1233826 7293.41602 74.1690063 6.53416395

07-Feb-06 11:31:00 191.1346741 7328.8457 74.207428 6.5344739

07-Feb-06 11:32:00 192.0785217 7380.8623 74.2458496 6.53478384

07-Feb-06 11:33:00 192.4195251 7348.30811 74.2842712 6.53509378

07-Feb-06 11:34:00 191.7227631 7323.82764 74.3226852 6.53540373

07-Feb-06 11:35:00 192.2797852 7321.32422 74.3611069 6.53571367

07-Feb-06 11:36:00 191.8362274 7357.11816 74.3995285 6.53602409

07-Feb-06 11:37:00 191.5427094 7366.62158 74.4379501 6.53633404

07-Feb-06 11:38:00 191.8920441 7337.2876 74.4763718 6.53664398

07-Feb-06 11:39:00 191.7332916 7322.31006 74.5147858 6.53695393

07-Feb-06 11:40:00 191.8720551 7322.67969 74.5532074 6.53726387

07-Feb-06 11:41:00 192.2187805 7326.34766 74.591629 6.53757381

07-Feb-06 11:42:00 192.2468262 7333.31494 74.6300507 6.53788376

07-Feb-06 11:43:00 192.1272125 7335.94531 74.6684647 6.53819418

07-Feb-06 11:44:00 191.8057556 7334.23877 74.5054474 6.53850412

07-Feb-06 11:45:00 191.6240387 7332.53223 74.4971466 6.53881407

Page 4 of 8
PI Ops Data

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

07-Feb-06 11:46:00 192.0630493 7330.82568 74.9818649 6.53912401

07-Feb-06 11:47:00 191.6002045 7329.11914 74.9204712 6.53943396

07-Feb-06 11:48:00 191.9951782 7327.41309 74.8590775 6.5397439

07-Feb-06 11:49:00 191.5269318 7314.09521 74.7976837 6.54005384

07-Feb-06 11:50:00 191.6515045 7297.26318 74.7362823 6.54036379

07-Feb-06 11:51:00 191.1468964 7337.10303 74.7288971 6.54067421

07-Feb-06 11:52:00 191.6325989 7360.55762 74.883522 6.54098415

07-Feb-06 11:53:00 192.360321 7339.04297 75.038147 6.5412941

07-Feb-06 11:54:00 192.0806122 7317.52832 75.1927719 6.54160404

07-Feb-06 11:55:00 191.392868 7323.35547 75.0221786 6.54191399

07-Feb-06 11:56:00 191.2852783 7397.20459 75.1248398 6.54222393

07-Feb-06 11:57:00 191.5014038 7370.89941 75.2275009 6.54253387

07-Feb-06 11:58:00 191.6573944 7338.79297 75.0509338 6.54284382

07-Feb-06 11:59:00 191.3853912 7330.11621 75.4587326 6.54315424

07-Feb-06 12:00:00 191.0116577 7324.84326 75.8665314 6.54346418

07-Feb-06 12:01:00 190.8314056 7328.62598 76.239006 6.54377413

07-Feb-06 12:02:00 191.6056671 7320.26758 76.117012 6.54408407

07-Feb-06 12:03:00 191.4607849 7318.15869 75.995018 6.53987885

07-Feb-06 12:04:00 191.315918 7317.79199 75.8730164 6.5356741

07-Feb-06 12:05:00 191.7461548 7307.3418 75.7510223 6.53146887

07-Feb-06 12:06:00 191.0330505 7318.25049 75.6290283 6.52726412

07-Feb-06 12:07:00 191.7238464 7333.83447 75.7658157 6.52305889

07-Feb-06 12:08:00 191.4428711 7365.95215 75.9210815 6.51885366

07-Feb-06 12:09:00 191.7355499 7375.31787 75.7127914 6.51464891

07-Feb-06 12:10:00 192.1906433 7380.08496 75.8148956 6.50690222

07-Feb-06 12:11:00 191.0988617 7427.39844 75.9169998 6.29022074

07-Feb-06 12:12:00 191.7406464 7437.77832 76.4647293 6.07688808

07-Feb-06 12:13:00 191.9567871 7410.71777 76.3110428 6.06112003

07-Feb-06 12:14:00 192.1729126 7346.94727 76.3877258 6.04535246

07-Feb-06 12:15:00 191.5245209 7322.94287 76.4644012 6.02958441

07-Feb-06 12:16:00 191.6937714 7390.21582 76.5410843 6.01381636

07-Feb-06 12:17:00 191.8768921 7307.39551 76.6177673 5.99804878

07-Feb-06 12:18:00 190.974762 7263.29736 76.6944504 5.98228073

07-Feb-06 12:19:00 191.0355225 7279.49219 76.7711334 5.96651268

07-Feb-06 12:20:00 191.1706085 7254.96143 76.8478165 5.95074511

07-Feb-06 12:21:00 190.9497833 7255.3584 76.560257 5.93497705

07-Feb-06 12:22:00 190.1144257 7239.95801 76.9709091 5.919209

07-Feb-06 12:23:00 190.5642395 7232.979 77.1249008 5.90344143

07-Feb-06 12:24:00 190.6993256 7251.75928 77.0046844 5.88767338

07-Feb-06 12:25:00 190.8344116 7256.8501 77.0508118 5.87190533

Page 5 of 8
PI Ops Data

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

07-Feb-06 12:26:00 190.9241333 7265.85156 77.0427704 5.85613775

07-Feb-06 12:27:00 191.0013123 7249.88477 77.0222397 5.8403697

07-Feb-06 12:28:00 191.0080719 7246.45361 77.1864929 5.82460165

07-Feb-06 12:29:00 190.9363251 7272.2002 77.4996185 5.80883408

07-Feb-06 12:30:00 190.6751556 7261.42432 77.6697922 5.79337025

07-Feb-06 12:31:00 191.0834045 7305.67676 77.3634796 5.79585981

07-Feb-06 12:32:00 190.6339569 7332.99512 77.0571594 5.79834938

07-Feb-06 12:33:00 190.7735443 7286.14844 76.9986267 5.80083942

07-Feb-06 12:34:00 190.3050385 7251.93994 77.5581665 5.80332899

07-Feb-06 12:35:00 190.8195953 7260.54102 77.710907 5.80581856

07-Feb-06 12:36:00 191.0744019 7350.4375 77.6039886 5.80830812

07-Feb-06 12:37:00 191.4274139 7341.58984 77.1355896 5.81079769

07-Feb-06 12:38:00 191.3181 7300.87598 76.9828415 5.81328773

07-Feb-06 12:39:00 190.9672394 7303.53613 76.6988525 5.8157773

07-Feb-06 12:40:00 191.5496063 7313.23926 76.3986511 5.81826687

07-Feb-06 12:41:00 191.1195679 7296.1748 75.934021 5.82075644

07-Feb-06 12:42:00 191.0581512 7290.65869 75.934021 5.82324648

07-Feb-06 12:43:00 191.0864563 7265.82471 76.1006775 5.82573605

07-Feb-06 12:44:00 191.0505066 7269.40625 76.8498917 5.82822561

07-Feb-06 12:45:00 190.6607513 7272.98779 76.6933289 5.83071518

07-Feb-06 12:46:00 191.1077881 7276.56934 76.2060776 5.83320475

07-Feb-06 12:47:00 190.9682159 7280.15088 75.9699554 5.83569479

07-Feb-06 12:48:00 191.1983032 7288.2041 76.2063599 5.83818436

07-Feb-06 12:49:00 191.8518677 7300.30469 75.7985611 5.84067392

07-Feb-06 12:50:00 191.6623077 7289.97363 75.3907623 5.84316349

07-Feb-06 12:51:00 191.0696716 7322.00684 75.3214264 5.84565306

07-Feb-06 12:52:00 190.6565552 7364.08887 75.4699249 5.8481431

07-Feb-06 12:53:00 191.576767 7323.49854 75.6184235 5.85063267

07-Feb-06 12:54:00 191.5561676 7283.83984 76.5294571 5.85312223

07-Feb-06 12:55:00 191.0885468 7293.39355 76.560257 5.8556118

07-Feb-06 12:56:00 191.5198669 7345.68896 75.9750824 5.85810137

07-Feb-06 12:57:00 192.5502777 7351.36768 75.934021 5.86059141

07-Feb-06 12:58:00 191.5783997 7314.38184 75.691597 5.86308098

07-Feb-06 12:59:00 191.8723145 7317.31543 75.8952026 5.86557055

07-Feb-06 13:00:00 190.9351196 7324.26318 76.2057343 5.86806011

07-Feb-06 13:01:00 191.9304047 7338.55371 76.1958084 5.87055016

07-Feb-06 13:02:00 191.4748688 7329.22021 76.1876221 5.87303972

07-Feb-06 13:03:00 191.0193176 7307.30078 76.4981537 5.87552929

07-Feb-06 13:04:00 191.2298889 7309.74512 77.23526 5.87801886

07-Feb-06 13:05:00 190.7212982 7312.18994 77.6972427 5.88050842

Page 6 of 8
PI Ops Data

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

07-Feb-06 13:06:00 191.6824188 7317.82861 77.8127365 5.88299847

07-Feb-06 13:07:00 190.9794922 7327.16064 77.1612473 5.88548803

07-Feb-06 13:08:00 191.2124176 7314.14355 77.3013077 5.887918

07-Feb-06 13:09:00 191.1034546 7296.46338 77.3969574 5.88684082

07-Feb-06 13:10:00 191.149292 7281.42969 77.7049408 5.88576412

07-Feb-06 13:11:00 190.1622925 7345.82666 77.5642853 5.88468695

07-Feb-06 13:12:00 190.9564667 7373.06104 77.6663895 5.88360977

07-Feb-06 13:13:00 190.4791412 7335.5376 77.7684937 5.8825326

07-Feb-06 13:14:00 191.0767517 7298.01416 77.6963882 5.88145542

07-Feb-06 13:15:00 191.3264465 7290.86523 77.491066 5.88037825

07-Feb-06 13:16:00 190.9606476 7372.64893 77.2857437 5.87930107

07-Feb-06 13:17:00 190.8740845 7324.62451 77.3456268 5.8782239

07-Feb-06 13:18:00 190.7875061 7296.02344 77.6536102 5.8771472

07-Feb-06 13:19:00 190.8662262 7270.41699 77.4996185 5.87607002

07-Feb-06 13:20:00 190.3953857 7286.73438 77.4996185 5.87499285

07-Feb-06 13:21:00 190.8666687 7299.71484 77.1865005 5.87391567

07-Feb-06 13:22:00 190.7293396 7268.11914 77.6248627 5.8728385

07-Feb-06 13:23:00 190.8137665 7266.46924 77.5468445 5.87176132

07-Feb-06 13:24:00 190.9866333 7266.54492 77.6700363 5.87068415

07-Feb-06 13:25:00 190.9321594 7289.11475 77.7932358 5.86961651

07-Feb-06 13:26:00 190.2860565 7293.33154 77.9164276 5.86908865

07-Feb-06 13:27:00 190.3977051 7300.35254 78.0396271 5.86856127

07-Feb-06 13:28:00 190.9952698 7336.04053 77.9014587 5.86803389

07-Feb-06 13:29:00 190.6485138 7341.17383 77.8319855 5.86750603

07-Feb-06 13:30:00 191.2536774 7347.57861 77.9089813 5.86697865

07-Feb-06 13:31:00 191.0563965 7382.68945 77.9859848 5.86645126

07-Feb-06 13:32:00 191.6238861 7428.4248 78.0629807 5.8659234

07-Feb-06 13:33:00 190.9552307 7382.74316 77.9256668 5.86539602

07-Feb-06 13:34:00 191.3014984 7321.41602 78.1027603 5.86486864

07-Feb-06 13:35:00 190.6795349 7294.59375 77.9487686 5.86434078

07-Feb-06 13:36:00 191.2492676 7370.85107 77.8308487 5.8638134

07-Feb-06 13:37:00 190.8860626 7308.66699 77.9861221 5.86328602

07-Feb-06 13:38:00 190.2096558 7251.43506 78.4326172 5.86275864

07-Feb-06 13:39:00 190.6796722 7263.53564 78.3562469 5.86223078

07-Feb-06 13:40:00 190.0146484 7275.63574 78.2798767 5.8617034

07-Feb-06 13:41:00 190.5704651 7285.75635 78.2035065 5.86117601

07-Feb-06 13:42:00 190.8991699 7268.15576 78.1271362 5.86064816

07-Feb-06 13:43:00 191.129776 7251.26416 78.7416611 5.86012077

07-Feb-06 13:44:00 190.8372955 7245.23389 78.7418289 5.85959339

07-Feb-06 13:45:00 190.4442291 7250.85693 78.4389801 5.85906553

Page 7 of 8
PI Ops Data

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

07-Feb-06 13:46:00 190.1539307 7242.58643 78.4389801 5.85853815

07-Feb-06 13:47:00 189.9719238 7260.48096 78.4389801 5.85801077

07-Feb-06 13:48:00 189.7588654 7231.14551 78.2165451 5.85748291

07-Feb-06 13:49:00 190.5630493 7230.41211 78.3192062 5.85695553

Page 8 of 8
APPENDIX C 

FUEL ANALYSIS 

Source: Unit 1

CALCULATION OF DENSITY AND HEATING VALUE @ 60°F and 30 in Hg

% volume Component Gross 

*

Volume

% Molecular Density 

*

x Gross Weight Heating Value Fract.

Component Volume Wt. (lb/ft3) Density weight % Btu/lb Fract. Btu (Btu/SCF) Btu

Hydrogen 35.8300 2.016 0.0053 0.00190 3.3695 61100 2058.77 325.0 116.4475Oxygen 0.0000 32.000 0.0846 0.00000 0.0000 0 0.00 0.0 0Argon 0.9770 39.948 0.1065 0.00104 1.8462 0 0.00 0.0 0Nitrogen 2.6000 28.016 0.0744 0.00193 3.4323 0 0.00 0.0 0CO2 15.4900 44.010 0.1170 0.01812 32.1574 0 0.00 0.0 0CO 45.0500 28.010 0.0740 0.03334 59.1521 4347 2571.34 322.0 145.061COS 0.0000 60.070 0.1602 0.00000 0.0000 0 0.00 0.0 0Methane 0.0563 16.041 0.0424 0.00002 0.0424 23879 10.11 1013.0 0.570319Ethane 0.000 30.067 0.0803 0.00000 0.0000 22320 0.00 1792.0 0Ethylene 0.000 28.051 0.0746 0.00000 0.0000 21644 0.00 1614.0 0Propane 0.000 44.092 0.1196 0.00000 0.0000 21661 0.00 2590.0 0propylene 0.000 42.077 0.1110 0.00000 0.0000 21041 0.00 2336.0 0Isobutane 0.000 58.118 0.1582 0.00000 0.0000 21257 0.00 3363.0 0n-butane 0.000 58.118 0.1582 0.00000 0.0000 21308 0.00 3370.0 0Isobutene 0.000 56.102 0.1480 0.00000 0.0000 20730 0.00 3068.0 0Isopentane 0.000 72.144 0.1904 0.00000 0.0000 21052 0.00 4008.0 0n-pentane 72.144 0.1904 0.00000 0.0000 21091 0.00 4016.0 0n-hexane 86.169 0.2274 0.00000 0.0000 20940 0.00 4762.0 0H2S 34.076 0.0911 0.00000 0.0000 7100 0.00 647.0 0

Total: 100.00 Average Density 0.05636 100.0000 Gross Heating Value

Specific Gravity 0.73671 Btu/lb 4640 Btu/SCF 262.08

Btu/lb 4327 Btu/SCF 244

*

 Density (lb/ft3) and Gross Heating Value (Btu/scf) data from Perry's Chemical Engineering Hanbook.

Net Heating Value (Lower Heating Value), Btu/lb, calculated as Gross Heating Value (Higher Heating Value) - 10.30 (%H2 x 8.94)

Net Heating Values

Coal Derived Gas and Heating Value Calculations

Customer: Tampa Electric Company Sample ID: Polk GC

Facility: Polk Power Station Analysis Date: 2/7/2006
Facility: Polk Power Station Analysis Date: 2/7/2006

Source: Unit 1

CALCULATION OF F FACTORS 

Weight Percents

Component Mol. Wt. C Factor H Factor % volume Fract. Wt. Carbon Hydrogen Nitrogen Oxygen

Hydrogen 2.016 0 1 35.830 72.2333 3.393508

Oxygen 32.000 0 0 0.000 0.0000 0

Argon 39.948 0 0 0.977 39.0292Nitrogen 28.016 0 0 2.600 72.8416 3.422086733

CO2 44.010 0.272273 0 15.490 681.7149 8.72004847 23.283525CO 28.010 0.42587 0 45.050 1261.8505 25.2462273 34.069098

COS 60.070 0.1998 0 0.000 0.0000 0 0Methane 16.041 0.75 0.25 0.056 0.9031 0.03182091 0.010607Ethane 30.067 0.8 0.2 0.000 0.0000 0 0Ethylene 28.051 0.85714 0.14286 0.000 0.0000 0 0Propane 44.092 0.81818 0.181818 0.000 0.0000 0 0Propene 42.077 0.85714 0.14286 0.000 0.0000 0 0Isobutane 58.118 0.82759 0.17247 0.000 0.0000 0 0n-butane 58.118 0.82759 0.17247 0.000 0.0000 0 0Isobutene 56.102 0.85714 0.14286 0.000 0.0000 0 0Isopentane 72.144 0.83333 0.16667 0.000 0.0000 0 0n-pentane 72.144 0.83333 0.16667 0.000 0.0000 0 0n-hexane 86.169 0.83721 0.16279 0.000 0.0000 0 0H2S 34.076 0 0.0586923 0.000 0.0000 0 0Totals 100.00330 2128.5726 33.9980967 3.40 3.422086733 57.352623

CALCULATED VALUES

O2 F Factor (dry), Fd 8298 DSCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air

O2 F Factor (wet), Fw 9714 SCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air

Moisture F Factor 1416 SCF of Water/MM Btu of Fuel Burned @ 0% excess airCombust. Moisture 14.58 volume % water in flue gas @ 0% excess air

CO2 F Factor, Fc 2352 DSCF of CO2/MM Btu of Fuel Burned @ 0% excess airCarbon Dioxide 28.34 volume % CO2 in flue gas @ 0% O2

Predicted Fo Factor 0.74 EPA Method 3a Fo value

Coal Derived Gas and Heating Value Calculations

Customer: Tampa Electric Company Sample ID: Polk GC
APPENDIX D 

CEMS DATA 
CEMS Data

Record# DATE TIME SO211 NOX12 CO213 OXY14

1 2/7/2006 91200 42.09 17.1 8.8 10.5

2 2/7/2006 91300 41.26 17.2 8.8 10.5

3 2/7/2006 91400 41.91 17.2 8.8 10.5

4 2/7/2006 91500 42.39 17.2 8.8 10.5

5 2/7/2006 91600 43.11 17.2 8.8 10.5

6 2/7/2006 91700 44.21 17.3 8.8 10.5

7 2/7/2006 91800 44.63 17.4 8.8 10.5

8 2/7/2006 91900 45.45 17.4 8.8 10.5

9 2/7/2006 92000 45.78 17.4 8.8 10.5

10 2/7/2006 92100 45.92 17.2 8.8 10.5

11 2/7/2006 92200 43.6 16.3 8.7 10.5

12 2/7/2006 92300 41.16 17.2 8.8 10.5

13 2/7/2006 92400 41.69 17.5 8.8 10.5

14 2/7/2006 92500 41.64 17.6 8.8 10.5

15 2/7/2006 92600 41.6 17.6 8.8 10.5

16 2/7/2006 92700 42.34 17.5 8.8 10.5

17 2/7/2006 92800 42.65 17.4 8.8 10.5

18 2/7/2006 92900 43.42 17.6 8.8 10.5

19 2/7/2006 93000 44.4 17.8 8.8 10.5

20 2/7/2006 93100 45.02 17.6 8.8 10.4

21 2/7/2006 93200 44.37 17.4 8.8 10.4

22 2/7/2006 93300 43.52 17.1 8.8 10.4

23 2/7/2006 93400 42.84 17 8.8 10.4

24 2/7/2006 93500 42.63 17 8.8 10.4

25 2/7/2006 93600 43.39 17.1 8.8 10.4

26 2/7/2006 93700 44.45 17.1 8.8 10.4

27 2/7/2006 93800 45.37 17.1 8.8 10.4

28 2/7/2006 93900 45.35 17 8.8 10.4

29 2/7/2006 94000 45.61 17 8.8 10.4

30 2/7/2006 94100 46.6 16.7 8.8 10.4

31 2/7/2006 94200 46.18 15.9 8.7 10.4

32 2/7/2006 94300 44.93 16.6 8.8 10.4

33 2/7/2006 94400 46.19 16.9 8.8 10.4

34 2/7/2006 94500 46.78 17 8.8 10.4

35 2/7/2006 94600 46.46 17.1 8.8 10.4

36 2/7/2006 94700 46.35 17.3 8.8 10.4

37 2/7/2006 94800 47.62 17.5 8.8 10.4

38 2/7/2006 94900 48.22 17.5 8.8 10.4

39 2/7/2006 95000 47.24 17.5 8.8 10.5

40 2/7/2006 95100 46.29 17.6 8.8 10.4

41 2/7/2006 95200 46.31 17.7 8.8 10.4

42 2/7/2006 95300 45.69 17.8 8.8 10.5

Page 1 of 7
CEMS Data

Record# DATE TIME SO211 NOX12 CO213 OXY14

43 2/7/2006 95400 44.74 17.6 8.8 10.5

44 2/7/2006 95500 44.35 17.5 8.8 10.5

45 2/7/2006 95600 44.27 17.6 8.8 10.5

46 2/7/2006 95700 45.22 17.6 8.8 10.5

47 2/7/2006 95800 46.29 17.7 8.8 10.5

48 2/7/2006 95900 46.69 17.9 8.8 10.5

49 2/7/2006 100000 46.94 18 8.7 10.5

50 2/7/2006 100100 47.52 17.8 8.7 10.4

51 2/7/2006 100200 47 17.2 8.7 10.5

52 2/7/2006 100300 44.91 18 8.7 10.5

53 2/7/2006 100400 44.31 18.1 8.7 10.5

54 2/7/2006 100500 43.63 18 8.7 10.5

55 2/7/2006 100600 42.94 17.9 8.7 10.5

56 2/7/2006 100700 43.96 17.8 8.7 10.5

57 2/7/2006 100800 45.48 17.8 8.7 10.5

58 2/7/2006 100900 47.36 17.9 8.7 10.5

59 2/7/2006 101000 47.98 18 8.7 10.5

60 2/7/2006 101100 48.12 18.1 8.7 10.5

61 2/7/2006 101200 47.64 18.2 8.7 10.5

62 2/7/2006 101300 47.05 18.3 8.7 10.5

63 2/7/2006 101400 44.9 18.4 8.7 10.5

64 2/7/2006 101500 42.96 18.3 8.7 10.5

65 2/7/2006 101600 42.64 18.3 8.7 10.5

66 2/7/2006 101700 42.37 18.3 8.7 10.5

67 2/7/2006 101800 43.35 18.3 8.7 10.5

68 2/7/2006 101900 44.77 18.4 8.7 10.5

69 2/7/2006 102000 45.14 18.4 8.7 10.5

70 2/7/2006 102100 46.73 18.3 8.7 10.5

71 2/7/2006 102200 47.69 17.1 8.7 10.5

72 2/7/2006 102300 46.51 17.8 8.8 10.5

73 2/7/2006 102400 46.49 18 8.8 10.5

74 2/7/2006 102500 46.28 18.2 8.7 10.5

75 2/7/2006 102600 46.03 18.3 8.8 10.5

76 2/7/2006 102700 44.27 18.3 8.8 10.5

77 2/7/2006 102800 43.39 18.5 8.7 10.5

78 2/7/2006 102900 43.93 18.6 8.7 10.5

79 2/7/2006 103000 45.33 18.5 8.7 10.5

80 2/7/2006 103100 45.33 18.5 8.7 10.5

81 2/7/2006 103200 45.51 18.3 8.8 10.5

82 2/7/2006 103300 44.41 18.2 8.8 10.5

83 2/7/2006 103400 43.87 18.2 8.7 10.5

84 2/7/2006 103500 43.57 18.2 8.7 10.5

Page 2 of 7
CEMS Data

Record# DATE TIME SO211 NOX12 CO213 OXY14

85 2/7/2006 103600 43.5 18.1 8.8 10.5

86 2/7/2006 103700 43.41 18 8.8 10.5

87 2/7/2006 103800 44.43 18 8.8 10.5

88 2/7/2006 103900 45.67 18.1 8.7 10.5

89 2/7/2006 104000 45.92 18.1 8.7 10.5

90 2/7/2006 104100 46.83 18 8.8 10.5

91 2/7/2006 104200 46.27 17.2 8.8 10.5

92 2/7/2006 104300 45.69 18 8.8 10.5

93 2/7/2006 104400 46.14 17.4 8.7 10.5

94 2/7/2006 104500 45.23 16.4 8.7 10.4

95 2/7/2006 104600 42.63 15.9 8.7 10.4

96 2/7/2006 104700 41.21 17.1 8.8 10.5

97 2/7/2006 104800 42.22 18.2 8.8 10.5

98 2/7/2006 104900 44.1 18.2 8.8 10.4

99 2/7/2006 105000 44.08 17.8 8.8 10.4

100 2/7/2006 105100 44.6 17.5 8.8 10.4

101 2/7/2006 105200 45.39 17.3 8.8 10.4

102 2/7/2006 105300 45.73 17.3 8.8 10.4

103 2/7/2006 105400 45.86 17.2 8.8 10.4

104 2/7/2006 105500 45.21 17.4 8.8 10.4

105 2/7/2006 105600 45.07 17.3 8.8 10.4

106 2/7/2006 105700 45.28 16.6 8.7 10.4

107 2/7/2006 105800 43.83 16.7 8.8 10.4

108 2/7/2006 105900 44.25 17.3 8.8 10.4

109 2/7/2006 110000 46.21 17.4 8.8 10.4

110 2/7/2006 110100 47.7 17.1 8.8 10.4

111 2/7/2006 110200 46.43 16.4 8.7 10.4

112 2/7/2006 110300 45.23 17.1 8.8 10.4

113 2/7/2006 110400 45.84 17.5 8.8 10.4

114 2/7/2006 110500 45.99 17.5 8.8 10.4

115 2/7/2006 110600 46.52 17.6 8.8 10.4

116 2/7/2006 110700 45.55 17.6 8.8 10.4

117 2/7/2006 110800 44.28 17.7 8.8 10.4

118 2/7/2006 110900 43.51 17.6 8.8 10.5

119 2/7/2006 111000 43.97 17.7 8.8 10.5

120 2/7/2006 111100 44.29 17.8 8.8 10.4

121 2/7/2006 111200 45.04 17.7 8.8 10.4

122 2/7/2006 111300 45.35 17.6 8.8 10.4

123 2/7/2006 111400 44.87 17.6 8.8 10.4

124 2/7/2006 111500 44.92 17.6 8.8 10.4

125 2/7/2006 111600 44.77 17.6 8.8 10.4

126 2/7/2006 111700 45.09 16.9 8.8 10.4

Page 3 of 7
CEMS Data

Record# DATE TIME SO211 NOX12 CO213 OXY14

127 2/7/2006 111800 43.85 17 8.8 10.4

128 2/7/2006 111900 43.63 17.7 8.8 10.5

129 2/7/2006 112000 44.57 17.8 8.8 10.5

130 2/7/2006 112100 45.45 17.9 8.8 10.4

131 2/7/2006 112200 45.37 16.9 8.8 10.4

132 2/7/2006 112300 45.06 17.4 8.8 10.5

133 2/7/2006 112400 45.08 17.5 8.8 10.4

134 2/7/2006 112500 45.01 17.4 8.8 10.5

135 2/7/2006 112600 44 17.5 8.8 10.4

136 2/7/2006 112700 43.42 17.6 8.8 10.5

137 2/7/2006 112800 43.48 17.8 8.8 10.5

138 2/7/2006 112900 44.72 17.9 8.8 10.5

139 2/7/2006 113000 45.78 18.1 8.8 10.5

140 2/7/2006 113100 46.81 18.1 8.8 10.5

141 2/7/2006 113200 47.94 17.9 8.8 10.5

142 2/7/2006 113300 48.32 18 8.8 10.5

143 2/7/2006 113400 48.03 17.9 8.8 10.5

144 2/7/2006 113500 46.89 17.8 8.8 10.5

145 2/7/2006 113600 44.93 17.8 8.8 10.4

146 2/7/2006 113700 44.25 17.1 8.8 10.4

147 2/7/2006 113800 41.86 17 8.8 10.4

148 2/7/2006 113900 40.98 17.7 8.8 10.5

149 2/7/2006 114000 42.68 17.8 8.8 10.5

150 2/7/2006 114100 44.14 17.9 8.8 10.4

151 2/7/2006 114200 45.92 17 8.8 10.5

152 2/7/2006 114300 45.7 17.6 8.8 10.5

153 2/7/2006 114400 44.91 17.9 8.8 10.5

154 2/7/2006 114500 44.36 17.8 8.8 10.5

155 2/7/2006 114600 43.88 17.8 8.8 10.5

156 2/7/2006 114700 43.54 17.7 8.8 10.5

157 2/7/2006 114800 42.86 17.7 8.8 10.5

158 2/7/2006 114900 41.22 17.7 8.8 10.5

159 2/7/2006 115000 41.1 17.8 8.8 10.4

160 2/7/2006 115100 42.43 17.7 8.8 10.4

161 2/7/2006 115200 43.09 17.7 8.8 10.5

162 2/7/2006 115300 44.28 17.8 8.8 10.5

163 2/7/2006 115400 45.03 18 8.8 10.5

164 2/7/2006 115500 45.17 18 8.8 10.5

165 2/7/2006 115600 44.98 18 8.8 10.5

166 2/7/2006 115700 45.15 17.3 8.8 10.4

167 2/7/2006 115800 43.07 17.2 8.8 10.5

168 2/7/2006 115900 41.27 17.7 8.8 10.5

Page 4 of 7
CEMS Data

Record# DATE TIME SO211 NOX12 CO213 OXY14

169 2/7/2006 120000 41.33 17.9 8.8 10.5

170 2/7/2006 120100 43.42 17.9 8.8 10.4

171 2/7/2006 120200 43.48 17 8.8 10.5

172 2/7/2006 120300 42.28 17.7 8.8 10.5

173 2/7/2006 120400 43.19 17.9 8.8 10.5

174 2/7/2006 120500 43.47 18 8.8 10.5

175 2/7/2006 120600 43.01 18 8.8 10.5

176 2/7/2006 120700 43.78 17.8 8.8 10.5

177 2/7/2006 120800 42.85 17.7 8.8 10.4

178 2/7/2006 120900 42.95 17.5 8.8 10.4

179 2/7/2006 121000 44.34 17.3 8.8 10.4

180 2/7/2006 121100 45.29 17.3 8.8 10.4

181 2/7/2006 121200 46.22 17.2 8.7 10.4

182 2/7/2006 121300 46.22 17.2 8.8 10.4

183 2/7/2006 121400 45.62 17.2 8.8 10.4

184 2/7/2006 121500 44.67 17.1 8.8 10.4

185 2/7/2006 121600 44.22 16.9 8.8 10.4

186 2/7/2006 121700 44.86 16.6 8.8 10.4

187 2/7/2006 121800 44.04 16.9 8.8 10.4

188 2/7/2006 121900 45.16 17.5 8.8 10.4

189 2/7/2006 122000 47.08 17.7 8.8 10.4

190 2/7/2006 122100 49.18 17.7 8.8 10.4

191 2/7/2006 122200 48.88 17.2 8.8 10.4

192 2/7/2006 122300 47.67 17.7 8.8 10.5

193 2/7/2006 122400 49.29 17.9 8.7 10.5

194 2/7/2006 122500 49.94 18.2 8.8 10.5

195 2/7/2006 122600 40.08 12.3 3.8 10.5

196 2/7/2006 122700 3.99 0.4 0.1 10.5

197 2/7/2006 122800 16.92 10.9 6.3 10.5

198 2/7/2006 122900 43.15 18.3 8.6 10.5

199 2/7/2006 123000 44.83 18.4 8.7 10.5

200 2/7/2006 123100 44.64 18.4 8.7 10.5

201 2/7/2006 123200 44.51 18.4 8.7 10.5

202 2/7/2006 123300 44.22 18.4 8.7 10.5

203 2/7/2006 123400 44.39 18.4 8.7 10.5

204 2/7/2006 123500 43.66 18.4 8.7 10.5

205 2/7/2006 123600 44.24 18.5 8.7 10.5

206 2/7/2006 123700 44.39 18.1 8.7 10.5

207 2/7/2006 123800 42.95 18.1 8.8 10.5

208 2/7/2006 123900 41.77 18.7 8.8 10.5

209 2/7/2006 124000 42.5 18.8 8.8 10.5

210 2/7/2006 124100 44.3 18.6 8.8 10.5

Page 5 of 7
CEMS Data

Record# DATE TIME SO211 NOX12 CO213 OXY14

211 2/7/2006 124200 44.7 17.7 8.8 10.5

212 2/7/2006 124300 43.92 18.2 8.8 10.5

213 2/7/2006 124400 44.8 18.4 8.8 10.5

214 2/7/2006 124500 45.58 18.5 8.8 10.5

215 2/7/2006 124600 45.97 18.8 8.8 10.5

216 2/7/2006 124700 45.88 18.5 8.8 10.5

217 2/7/2006 124800 43.8 18.6 8.8 10.5

218 2/7/2006 124900 43.88 18.7 8.8 10.5

219 2/7/2006 125000 45.51 18.7 8.8 10.5

220 2/7/2006 125100 46.37 18.7 8.8 10.5

221 2/7/2006 125200 45.69 18.6 8.8 10.5

222 2/7/2006 125300 45.6 18.6 8.8 10.5

223 2/7/2006 125400 46.12 18.6 8.8 10.5

224 2/7/2006 125500 47.71 18.6 8.7 10.5

225 2/7/2006 125600 49.45 18.5 8.7 10.5

226 2/7/2006 125700 49.88 18.1 8.8 10.5

227 2/7/2006 125800 48.62 17.8 8.8 10.5

228 2/7/2006 125900 47.1 18.3 8.8 10.5

229 2/7/2006 130000 47.06 18.5 8.8 10.5

230 2/7/2006 130100 47.92 18.5 8.8 10.5

231 2/7/2006 130200 48.29 17.7 8.8 10.5

232 2/7/2006 130300 47 18.1 8.8 10.5

233 2/7/2006 130400 46.87 18.5 8.8 10.5

234 2/7/2006 130500 45.02 18.5 8.8 10.5

235 2/7/2006 130600 42.29 18.3 8.8 10.5

236 2/7/2006 130700 39.62 18.2 8.8 10.5

237 2/7/2006 130800 36.15 18.2 8.8 10.5

238 2/7/2006 130900 34.34 18.1 8.8 10.5

239 2/7/2006 131000 32.94 18.1 8.8 10.5

240 2/7/2006 131100 32.03 17.8 8.8 10.4

241 2/7/2006 131200 30.57 17.8 8.8 10.5

242 2/7/2006 131300 30.35 18 8.8 10.5

243 2/7/2006 131400 31.17 18.1 8.8 10.5

244 2/7/2006 131500 33.94 18.2 8.7 10.5

245 2/7/2006 131600 36.17 18.2 8.8 10.5

246 2/7/2006 131700 35.49 17.8 8.8 10.4

247 2/7/2006 131800 31.64 17.4 8.8 10.5

248 2/7/2006 131900 29.96 17.9 8.8 10.5

249 2/7/2006 132000 30.51 18.1 8.8 10.5

250 2/7/2006 132100 32.84 18.2 8.8 10.4

251 2/7/2006 132200 35.24 17.5 8.7 10.4

252 2/7/2006 132300 35.16 17.8 8.8 10.5

Page 6 of 7
CEMS Data

Record# DATE TIME SO211 NOX12 CO213 OXY14

253 2/7/2006 132400 34.28 18.1 8.8 10.5

254 2/7/2006 132500 34.91 18.2 8.8 10.5

255 2/7/2006 132600 35.54 18.1 8.8 10.4

256 2/7/2006 132700 34.84 17.9 8.8 10.4

257 2/7/2006 132800 35.55 17.8 8.7 10.4

258 2/7/2006 132900 37.36 17.7 8.7 10.4

259 2/7/2006 133000 38.28 17.6 8.7 10.4

260 2/7/2006 133100 38.33 17.6 8.7 10.4

261 2/7/2006 133200 37.74 17.5 8.7 10.4

262 2/7/2006 133300 38.17 17.5 8.7 10.4

263 2/7/2006 133400 39.48 17.3 8.7 10.4

264 2/7/2006 133500 40.08 17.2 8.7 10.4

265 2/7/2006 133600 42.56 17.1 8.7 10.4

266 2/7/2006 133700 44.32 16.8 8.7 10.4

267 2/7/2006 133800 43.42 16.7 8.8 10.4

268 2/7/2006 133900 41.85 17.3 8.8 10.4

269 2/7/2006 134000 43.31 17.5 8.8 10.4

270 2/7/2006 134100 43.49 17.6 8.8 10.4

271 2/7/2006 134200 42.63 17.3 8.8 10.4

272 2/7/2006 134300 42.07 17.6 8.7 10.4

273 2/7/2006 134400 42.01 17.8 8.7 10.4

274 2/7/2006 134500 42.39 17.9 8.7 10.4

275 2/7/2006 134600 42.13 17.9 8.7 10.4

276 2/7/2006 134700 41.01 17.8 8.7 10.4

277 2/7/2006 134800 40.55 17.9 8.7 10.4

278 2/7/2006 134900 40.41 17.9 8.7 10.4

279 / /

280 / / AVE 43.467 17.619 8.716 10.462

Page 7 of 7
APPENDIX F 

TEST PARTICIPANTS 
TEST PARTICIPANTS

AIR SERVICES GROUP 

ENVIRONMENTAL SERVICES

Robert Barthelette Environmental Technician 

Charles Dufeny Environmental Technician 

Juan Ramirez Environmental Technician 

Jorge Varino Technician 

POLK POWER STATION

Michael Perkins Environmental Coordinator