Name: Gregory D. Smith

Title: Plant Manager

Company: Public Service Company of New Mexi

Sign Date: 12/7/2010

Name: Karl G. Breuer

Title: Technical Report Writer

Company: Air Pollution Testing, Inc.

Sign Date: 6/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

San Juan Generating Station ICR Test

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Saturday, February 26, 2011 Page 1 of 21
San Juan Generating Station ICR Test

12/7/2010

Facility Information:

San Juan Unit 4

6800 North County Road

Waterflow NM 87421

Contact: Rod Seagle

Phone: (598) 505-7529

Fax: (505) 598-7247

Email: rodney.seagle@pnmresources.com

Testing Company:

Air Pollution Testing, Inc.

5530 Marshall Street

Arvada CO 80002

Contact: Karl Breuer

Phone: (303) 420-5949

Fax:

Email: kbreuer@airtest.net

Air Permit Number:

P062R1M1

Permitted Source ID/Name:

SJGS 4 San Juan Generating Station

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Coal fired generating unit burning subbituminuous coal. Controls include, Baghouse, Activated Carbon Injection, 

and an FGD.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000600868 FRS #: 110000600868

SCC / Description 10100222 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Subbituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Unit 4 Stack 

House

350 0 0 0 2.74 6.51 4 16

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Unit 4 Stack Hydrogen Chloride Method 26A 3 192 0

House

Unit 4 Stack Hydrogen Fluoride Method 26A 3 192 0

House

Unit 4 Stack Cadmium Method 29 3 256 0

House

Saturday, February 26, 2011 Page 2 of 21
San Juan Generating Station ICR Test

12/7/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

No deviations were implemented as part of this test program.

Unit 4 Stack Nickel Method 29 3 256 0

House

Unit 4 Stack Arsenic Method 29 3 256 0

House

Unit 4 Stack Chromium Method 29 3 256 0

House

Unit 4 Stack Cobalt Method 29 3 256 0

House

Unit 4 Stack Lead Method 29 3 256 0

House

Unit 4 Stack Manganese Method 29 3 256 0

House

Unit 4 Stack Antimony Method 29 3 256 0

House

Unit 4 Stack Selenium Method 29 3 256 0

House

Unit 4 Stack O2 Method 3A O2 3 60 0

House

Unit 4 Stack Co2 Method 3A CO2 3 60 0

House

Organic Condensible 

Particulate

Unit 4 Stack Method 5/OTM-28 3 256 0

House

Inorganic (Aqueous) 

Condensible Part.

Unit 4 Stack Method 5/OTM-28 3 256 0

House

Unit 4 Stack Filterable Particulate Method 5/OTM-28 3 256 0

House

Unit 4 Stack Total Particulate Method 5/OTM-28 3 256 0

House

Saturday, February 26, 2011 Page 3 of 21
San Juan Generating Station ICR Test

12/7/2010

Sampling / Stack Data Results Summary

Location Unit 4 Stack House - Method 26A

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/21/2010

Run Start Time 8:59:00 AM 7:34:00 

AM

7:35:00 AM

Run Finish Time 2:28:00 PM 1:52:00 PM 12:42:00 PM

Net Run Time, minutes 192 192 192

Dry Gas Meter Volume Sampled, dscf 109.882 113.907 107.212 110.334

Moisture Content of Stack Gas, % 13.76 13.21 14.19 13.720

Moisture Saturation at Stack Gas Temperature, % 11.95 11.73 11.76 11.813

Carbon Dioxide, % 13.5 13.5 13.6 13.533

Oxygen, % 5.7 5.5 5.5 5.567

Average Stack Gas Temperature, °F 114.31 113.69 113.69 113.897

Dry Volumetric Flow Rate, dry scfm 1,028,599.6 1,037,023.6 1,026,136.5 1,030,586.56

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,548,601.0 1,553,812.4 1,541,786.0 1,548,066.46

7

Percent Isokinetic of Sampling Rate, % 103.2 106.1 100.9 103.400

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, February 26, 2011 Page 4 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Unit 4 Stack House - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 5 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 4 Stack House - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 6 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 4 Stack House - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, February 26, 2011 Page 7 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 4 Stack House - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Saturday, February 26, 2011 Page 8 of 21
San Juan Generating Station ICR Test

12/7/2010

Emissions Summary

Location: Unit 4 Stack House - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.455 0.455 0.417 0.442

lb/mmBtuO2 1.23E-04 1.17E-04 1.14E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.436 0.436 0.399 0.424

lb/mmBtuO2 1.18E-04 1.12E-04 1.09E-04 0.000

Location: Unit 4 Stack House - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0005 0.0009 0.0003 0.001

lb/mmBtuO2 1.01E-07 1.67E-07 5.54E-08 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.0004 0.0004 0.0005 0.000

lb/mmBtuO2 8.11E-08 7.41E-08 9.23E-08 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0029 0.0012 0.0004 0.002

lb/mmBtuO2 5.88E-07 2.22E-07 7.38E-08 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0079 0.036 0.0156 0.020

lb/mmBtuO2 1.60E-06 6.67E-06 2.88E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.0016 0.0031 0.0037 0.003

lb/mmBtuO2 3.24E-07 5.74E-07 6.83E-07 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0033 0.0024 0.0035 0.003

lb/mmBtuO2 6.69E-07 4.45E-07 6.46E-07 0.000

Saturday, February 26, 2011 Page 9 of 21
San Juan Generating Station ICR Test

12/7/2010

Process Run Data

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.009 0.0151 0.0071 0.010

lb/mmBtuO2 1.82E-06 2.80E-06 1.31E-06 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0068 0.0212 0.0069 0.012

lb/mmBtuO2 1.38E-06 3.93E-06 1.27E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0008 0.0009 0.001 0.001

lb/mmBtuO2 1.62E-07 1.67E-07 1.85E-07 0.000

Location: Unit 4 Stack House - Method 5/OTM-28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 15.15 18.65 13.35 15.717

lb/mmBtuO2 3.37E-03 3.50E-03 2.72E-03 0.003

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 2.7 8.6 9.6 6.967

lb/mmBtuO2 6.00E-04 1.61E-03 1.96E-03 0.001

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 9.5 4.8 9.9 8.067

lb/mmBtuO2 2.11E-03 9.01E-04 2.02E-03 0.002

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 27.35 32.05 32.85 30.750

lb/mmBtuO2 6.08E-03 6.01E-03 6.70E-03 0.006

Saturday, February 26, 2011 Page 10 of 21
San Juan Generating Station ICR Test

12/7/2010

Process Run Data

APCD Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 4655 mmBtu/hr 4660

2 Heat Input 0 mmBtu/hr 4660

3 Heat Input 0 mmBtu/hr 4660

1 Load 456 Mw 460

1 Steam Output 2732 Klbs/hr 2670

1 Stack Moisture 11.85 % 13

1 Stack Flow Rate 1E+06 dscfm 1E+06

1 Stack Temperature 122 deg F 115

1 Coal Flow Rate 461240 lbs/hr 460000

1 CO2 13.6 % 13.5

1 O2 5.7 % 5.7

4 Heat Input 4681 mmBtu/hr 4660

4 Load 457 Mw 460

4 Steam Output 2739 Klbs/hr 2670

4 Stack Moisture 11.66 % 13

4 Stack Flow Rate 1E+06 dscfm 1E+06

4 Stack Temperature 121 deg F 115

4 Coal Flow Rate 454410 lbs/hr 460000

4 CO2 13.7 % 13.5

4 O2 5.6 % 5.7 This is run 2

5 Heat Input 4763 mmBtu/hr 4660

5 Load 462 Mw 460

5 Steam Output 2768 Klbs/hr 2670

5 Stack Moisture 11.81 % 13

5 Stack Flow Rate 1E+06 dscfm 1E+06

5 Stack Temperature 122 deg F 115

5 Coal Flow Rate 459150 lbs/hr 460000

5 CO2 13.9 % 13.5

5 O2 5.4 % 5.7 This is run 3

Run Name Value UOM Comments

Target

Value

1 ACTIVATED CARBON ADSORPTION 0.15ACI Feed Rate #/macf 0.15

Saturday, February 26, 2011 Page 11 of 21
San Juan Generating Station ICR Test

12/7/2010

Process Lab Run Data

2 ACTIVATED CARBON ADSORPTION 0.15ACI Feed Rate #/macf 0.15

3 ACTIVATED CARBON ADSORPTION 0.15ACI Feed Rate #/macf 0.15

1 BAGHOUSE 99.99Removal Efficiency 99.99

2 BAGHOUSE 99.99Removal Efficiency 99.99

3 BAGHOUSE 99.99Removal Efficiency 99.99

1 SPRAY SCRUBBER 94.1Removal Efficiency 90

2 SPRAY SCRUBBER 94.1Removal Efficiency 90

3 SPRAY SCRUBBER 94.1Removal Efficiency 90

Run Name Value UOM Comments

1 Scrubber TDS mg/l

1 Scrubber TSS mg/l

1 Scrubber Delta Pressure 0.38 "H20

1 Scrubber Liquor Flow gal/min

2 Scrubber TDS mg/l

2 Scrubber TSS mg/l

2 Scrubber Delta Pressure 0.4 "H20

2 Scrubber Liquor Flow gal/min

3 Scrubber TDS mg/l

3 Scrubber TSS mg/l

3 Scrubber Delta Pressure 0.28 "H20

3 Scrubber Liquor Flow gal/min

Saturday, February 26, 2011 Page 12 of 21
San Juan Generating Station ICR Test

12/7/2010

Sampling / Stack Data Results Detail

Location Unit 4 Stack House - Method 26A

Average

Run Number 1 2 3

Test Date 5/19/2010 5/20/2010 5/21/2010

Run Start Time 8:59:00 AM 7:34:00 AM 7:35:00 AM

Run Finish Time 2:28:00 PM 1:52:00 PM 12:42:00 PM

Net Traversing Points 32 32 32

Net Run Time, minutes 192 192 192

Nozzle Diameter, inches 0.257 0.257 0.257 0.257

Pitot Tube Coefficient 0.83 0.83 0.83 0.830

Dry Gas Meter Calibration Factor 0.994 0.994 0.994 0.994

Barometric Pressure, inches of Mercury 24.6 24.63 24.57 24.600

Average Orifice Meter Differential, inches H2O 1.28 1.29 1.34 1.303

Dry Gas Meter Volume Sampled, cubic feet 136.385 141.312 133.737 137.145

Average Dry Gas Meter Temperature, °F 77.64 78.05 79.77 78.487

Dry Gas Meter Volume Sampled, dscf 109.882 113.907 107.212 110.334

Total Moisture Liquid collected, g 372.4 368.2 376.6 372.400

Volume of Water Vapor, standard cubic feet 17.53 17.33 17.73 17.530

Moisture Content of Stack Gas, % 13.76 13.21 14.19 13.720

Moisture Saturation at Stack Gas Temperature, % 11.95 11.73 11.76 11.813

Dry Mole Fraction 0.8805 0.8827 0.8824 0.882

Carbon Dioxide, % 13.5 13.5 13.6 13.533

Oxygen, % 5.7 5.5 5.5 5.567

Carbon Monoxide & Nitrogen, % 80.8 81 80.9 80.900

Fuel Factor 1.13 1.14 1.13

Dry Molecular Weight, lb/lb-Mole 30.39 30.38 30.40 30.390

Wet Molecular weight, lb/lb-Mole 29.24 29.19 29.38 29.270

Flue Gas Static Pressure, inches of H2O -0.65 -0.65 -0.65 -0.650

Absolute Flue Gas Pressure, inches of Mercury 24.55 24.58 24.52 24.550

Average Stack Gas Temperature, °F 114.31 113.69 113.69 113.897

Average Velocity Head, inches of H2O 0.3704596597

80894

0.373107399

472888

0.368942573

222379

0.371

Average Stack Gas Velocity, feet/second 38.63 38.76 38.46 38.617

Stack Cross-Sectional Area, square feet 668.134 668.134 668.134 668.134

Dry Volumetric Flow Rate, dry scfm 1,028,599.6 1,037,023.6 1,026,136.5 1,030,586.5

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,548,601.0 1,553,812.4 1,541,786.0 1,548,066.4

67

Percent Isokinetic of Sampling Rate, % 103.2 106.1 100.9 103.400

Percent Excess Air, % 36.5 34.6 34.7 35.267

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 350 350 350

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Saturday, February 26, 2011 Page 13 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, February 26, 2011 Page 14 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 15 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A CO2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 16 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A CO2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 17 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 18 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A O2 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 19 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 3A O2 3 6

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, February 26, 2011 Page 20 of 21
San Juan Generating Station ICR Test

12/7/2010

Location Unit 4 Stack House - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Saturday, February 26, 2011 Page 21 of 21