# Final Report

Testing for EPA Utility Boiler MACT

Information Collection Request (ICR)

Unit 1 and Unit 2 at

Southampton Power Station

Franklin, Virginia

Prepared for:

Dominion Generation

Emissions Monitoring and Support Group

1100 Coxendale Road

Chester, VA 23836-2549

Prepared by:

Wannalancit Mills

650 Suffolk Street

Lowell, Massachusetts 01854

(978) 970-5600



# June 2010

# TRC Project No. 170096

June 2010



# FINAL REPORT

Testing for EPA Utility Boiler MACT

Information Collection Request (ICR)

Unit 1 and Unit 2 at

Southampton Power Station

Franklin, Virginia

Prepared for

Dominion Generation

Emissions Monitoring and Support Group

1100 Coxendale Road

Chester, VA 23836-2549

Prepared by

TRC Environmental Corporation

Wannalancit Mills

650 Suffolk Street

Lowell, Massachusetts 01854

(978) 970-5600

DISCLAIMER

This report is intended for use solely by Dominion Genera tion for the specific purposes described in the contractual

documents between TRC Environmental Corporation (TRC) and Dominion Generation. All professional services

performed and reports generated by TRC have been prepar ed for Dominion Generation’s purposes as described in the

contract. The information, statements and conclusions contained in the report have been prepared in accordance with

the work statement and contra ct terms and conditions. The report may be subject to differing interpretations and/or

may be misinterpreted by third persons or entities who were not involved in the investigative or consultation process.

TRC therefore expressly disclaims any liability to persons other than Dominion Generation who may use or rely

upon this report in any way or for any purpose.

# TABLE OF CONTENTS

Section Page

L2010-275 

# ii 1.0 INTRODUCTION............................................................................................................. 1

1.1 OVERVIEW ........................................................................................................... 1

1.2 SCOPE OF WORK................................................................................................. 2

1.3 TEST METHODS AND PARAMETERS.............................................................. 4

1.4 PROCESS MONITORING .................................................................................... 5

1.5 FUEL SAMPLING ................................................................................................. 5

2.0 SUMMARY OF RESULTS ............................................................................................. 7

2.1. ACID GASES ......................................................................................................... 7

2.2 MERCURY AND NON-METALLICS.................................................................. 7

2.3 NON-DIOXIN FURANS........................................................................................ 8

3.0 FACILITY DESCRIPTION AND SAMPLING LOCATIONS................................. 10

3.1 FACILITY DESCRIPTION ................................................................................. 10

3.2 SAMPLING LOCATIONS .................................................................................. 10

3.3 STRATIFICATION TEST FOR SO 2, NOx, CO, O2 and CO2........................... 11

4.0 FIELD SAMPLING PROGRAM.................................................................................. 12

4.1 OVERVIEW ......................................................................................................... 12

4.2 FIELD PROGRAM DESCRIPTION ................................................................... 12

4.3 PRE-SAMPLING ACTIVITIES .......................................................................... 14

4.3.1 Equipment Calibration.............................................................................. 14

4.3.2 Glassware Preparation .............................................................................. 15

4.3.3 Sample Media Preparation........................................................................ 16

4.3.4 Continuous Emissions Monitoring ........................................................... 16

4.3.5 Interference Gas Test ................................................................................ 18

4.3.6 Determination of CEMS Response Time ................................................. 19

4.3.7 NO 2 

# to NO Conversion Efficiency ........................................................... 19

4.4 ONSITE SAMPLING ACTIVITIES.................................................................... 19

4.4.1 EPA Methods 1 and 2 for Velocity Measurements/Cyclonic Flow.......... 20

4.4.2 EPA Method 3A/3B for O2/CO2.............................................................. 20

4.4.3 EPA Method 4 for Moisture Determination ............................................. 21

4.4.4 EPA OTM 27/OTM 28 for Filterable PM and CPM ................................ 21

4.4.5 Continuous Emissions Monitoring for O 2 

# , CO 2 

# , SO 2 

# , NO

x 

# , and CO........ 25

4.4.6 EPA Method 18 for Methane.................................................................... 25

4.4.7 EPA Method 25A for Methane and Total Hydrocarbons (THC) ............. 26

4.4.8 EPA Method 26A/CTM-033 for HCl/HF/HCN ....................................... 27

4.4.9 EPA Method 29 for Metals....................................................................... 29

4.4.10 EPA Method 30B for Mercury ................................................................. 31

4.4.11 Method 0031 for Volatile Organics .......................................................... 32

4.4.12 Method 0010 for Semi-Volatile Organics/POM....................................... 34

4.4.13 Method 0011 for Formaldehyde ............................................................... 36

# TABLE OF CONTENTS

Section Page

L2010-275 

# iii 5.0 ANALYTICAL PROCEDURES AND CALCULATIONS ........................................ 46

5.1 ANALYTICAL PROCEDURES.......................................................................... 46

5.1.1 Particulate Matter (PM2.5 and CPM) ....................................................... 46

5.1.2 Metals........................................................................................................ 46

5.1.3 Mercury..................................................................................................... 47

5.1.4 HCl/HF/HCN ............................................................................................ 47

5.1.5 Volatile and Semi-Volatile Organics........................................................ 48

5.1.6 Formaldehyde ........................................................................................... 48

5.2 CALCULATIONS................................................................................................ 50

5.2.1 Flow Rates ................................................................................................ 50

5.2.1.1 Volume of Dry Gas Sample d at Standard Conditions ................. 50

5.2.1.2 Velocity of the Exhaust Gas ........................................................ 50

5.2.1.3 Volumetric Flow Rate of the Exhaust Gas .................................. 51

5.2.2 Particulate Matter - Grains per Dry Standard Cubic Foot ........................ 51

5.2.3 Particulate Matter – Po unds per Million BTU.......................................... 52

5.2.4 Vapor Phase Mercury Concentration........................................................ 52

5.2.5 Mass of Hydrogen Halides HCl and HF................................................... 53

5.2.6 Total Weight of HCN in Sample .............................................................. 53

5.2.7 Concentrations of HCl, HF, and HCN...................................................... 53

5.2.8 HCl, HF, and HCN – Pounds per Million BTU........................................ 54

5.2.9 Parts per Million Corrected to 7% Oxygen............................................... 54

5.2.10 Pounds per Million BTU........................................................................... 54

5.2.11 Formaldehyde ........................................................................................... 55

5.2.11.1 Total Formaldehyde................................................................ 55

5.2.11.2 Concentration.......................................................................... 55

5.2.12 CO, SO 2 

# and NO

x 

# – Pounds per Million BTU.......................................... 56

6.0 QUALITY ASSURANCE .............................................................................................. 57

6.1 OVERVIEW ......................................................................................................... 57

6.2 FIELD QUALITY CONTROL SUMMARY....................................................... 57

6.2.1 Calibration Procedures.............................................................................. 57

6.2.2 Equipment Leak Checks ........................................................................... 57

6.2.3 Calibration Gases...................................................................................... 58

6.2.4 Cyclonic Flow Check................................................................................ 58

6.2.5 Method Blanks.......................................................................................... 58

6.2.6 Spike Recovery (for Method 30B)............................................................ 58

6.3 SAMPLE CHAIN OF CUSTODY ....................................................................... 58

6.4 DATA REDUCTION, VALIDAT ION, AND REPORTING .............................. 59

6.4.1 Field Data Reduction ................................................................................ 59

6.4.2 Laboratory Analysis Data Reduction........................................................ 59

6.4.3 Data Validation ......................................................................................... 59

6.4.4 Data Reporting.......................................................................................... 60

# TABLE OF CONTENTS, continued

L2010-275 

# iv APPENDICES

A FIELD SAMPLING DATA SHEETS

B FIELD REDUCED DATA

C FACILITY PROCESS DATA

D LABORATORY ANALYTICAL DATA

E EQUIPMENT CALIBRATION SHEETS

TABLES

Number Page

1-1 Sample and Analytical Test Matrix .................................................................................... 3

1-2 List of Analytical Me thods and Fuel Analysis ................................................................... 6

2-1 Average Emission Rates of Acid Gase s from Unit 1 and Unit 2 Common Stack.............. 7

2-2 Average Emission Rates of Me rcury and Non-Metallic HAPs .......................................... 8

2-3 Average Emission Rates of Non-Dioxin Furans Unit 1 and Unit 2 Common Stack.......... 9

3-1 Sampling Traverse Sampling Points for Unit 1 and Unit 2 Common Stack .................... 10

4-1 Calibration Gas Values and Instrument Ranges for Methods 3A, 6C, 7E, and 10........... 18

4-2 Continuous Emissions Monito ring Performance Criteria................................................. 18

FIGURES

Number Page

4-1 Schematic of EPA OTM27/OTM 28 Sampling Train .......................................................39

4-2 Schematic of TRC CEM System .......................................................................................40

4-3 Schematic of EPA Method 29 Sampling Train..................................................................41

4-4 Schematic of EPA Method 30B Sampling Train...............................................................42

4-5 Schematic of SW-846 Method 0031 (SMVOC) Sampling Train......................................43

4-6 Schematic of SW-846 Method 0010 (Semi-Volatiles) Sampling Train ............................44

4-7 Schematic of SW-846 Method 0011 (HCOH) Sampling Train.........................................45

5-1 OTM 28 Sample Processing Flow Chart .......................................................................... 49

# L2010-275 

# 1 1.0 INTRODUCTION

1.1 OVERVIEW

TRC Environmental Corporation (TRC) of Lowell, Massachusetts was retained by Dominion to

perform EPA Utility MACT ICR testing at th e Southampton Power Station located at 30134

General Thomas Highway in Franklin, Virginia. Dominion requested and received authorization

to test the two units combined emissions in the common stack.

Testing was conducted for Unit 1 and Unit 2on th e common stack at the Southampton Power

Station and included Hazardous Air Pollutant (HAP) emissions sampling for acid gases

(hydrochloric acid (HCl), hydr ogen fluoride (HF), hydrogen cyan ide (HCN), sulfur dioxide

(SO2), and oxides of nitrogen (NOx)); Mercur y and Non-Mercury Meta llic HAPs (Hg, metals,

and particulate matter (PM) including condensab le particulate matter); and Non-Dioxin/Furan

Organics (volatile organics (VOCs), semi-volatile organics and POM, and formaldehyde

(HCOH). POM included organi c compounds with more than one benzene ring, and which have

a boiling point greater than 100 degrees Celsius. Triplicate te st runs were performed, and

volumetric flow rate, the moisture content of the stack gas, and oxygen and carbon dioxide

concentrations were also meas ured during each test run. Al l testing was conducted while the

units were operating at “normal” load under steady state conditions.

Sampling and analysis procedures described in this document we re conducted using procedures

deemed acceptable by the United States Environm ental Protection Agency (USEPA). TRC was

responsible for the collection and anal ysis of all flue gas samples.

Sampling and analysis were pe rformed under the direction of Mr. Michael Martin of TRC’s

Lowell, Massachusetts office. Mr. Ken Atkins of Dominion EMSG provide d process and testing

coordination at the facility.

# L2010-275 

# 2 1.2 SCOPE OF WORK

This section of the test report pr esents an overview of the scope of work and schedule associated

with the testing of the Unit 1 and Unit 2 at the Southampton Power Station. The sample and

analytical test matrix is presented in Table 1-1. The test program a pproach involved conducting

a series of three test runs at the common stack outlet for various pollutants, while the units were

operated at normal load under st eady-state conditions.

Testing was conducted for Acid Gases, includi ng: hydrochloric acid (HCl), hydrogen fluoride

(HF), hydrogen cyanide (HCN), sulfur dioxide (SO2), and oxides of nitrogen (NOx).

HCl/HF/HCN, NOx and SO2 results have been reported in lb/MMBtu, using Method 19

procedures. SO2 and NOx results have also be en reported as ppmvd@7% O2. Testing was also

conducted for mercury (Hg) and non-mercury meta llic HAPs including the following: metals,

particulate matter (PM 2.5 

# ), and condensable particulate matter. Hg, metals and all PM results

were reported as lb/MMBtu, us ing Method 19 procedures.

Additionally, the emissions of non-dioxin/furan organics were quantified. These included:

volatile organics (VOCs), semi-volatile orga nics and POM, formaldehyde (HCOH), total

hydrocarbons (THC), methane (CH4), carbon monoxi de (CO), and sulfur dioxide (SO2).

Volatile and semi-volatile organics results ha ve been reported as lb/MMBtu, using Method 19

procedures, and ug/dscm corrected to 7% O 2. THC, methane, formaldehyde, CO, and SO2

results have been reported as lb/MMBtu, us ing Method 19 procedures, and ppmvd @7% O2.

The operating conditions and corresponding test parameters are discussed below.

# L2010-275 

# 3 TABLE 1-1. SAMPLE AND ANALYTICAL TEST MATRIX



# Source Scope of

Work Test

Parameter Test Method No. of

Test

Runs Minimum

Run Time

Units 1 and 2

Common Stack Acid Gases 1 

# HCl, HF, HCN EPA Method

26A/CTM-033 3 3 hours

SO2 6 

# EPA 6C 3 3 hours

NOx EPA 7E 3 3 hours

O2/CO2 EPA 3A 3 3 hours

Unit 1 and 2

Common Stack Mercury and

Non-Mercury

Metallic 2 

# Metals/PM EPA 29 3 

# 3 4 hours

Mercury (Hg) EPA 30B 3 4 hours

PM &

Condensible OTM 27 /OTM

28 3 

# 3 4 hours

O2/CO2 EPA 3A or 3B 3 4 hours

Total Solids

(Scrubber

Liquid) ASTM D5907 3 4 hours

Unit 1 and 2

Common Stack NonDioxin/Furan

Organics 4 

# Volatile

Organics Method 0031 3 2 hours

Semi-Volatile

Organics/POM Method 0010 3 2 hours

Formaldehyde Method 0011 3 2 hours

Total

Hydrocarbons

(THC) EPA 25A 3 2 hours

Methane 5 

# EPA 18 3 2 hours

CO EPA 10 3 2 hours

SO2 6 

# EPA 6C 3 2 hours

O2/CO2 EPA 3A 3 2 hours

1 During testing for acid gases, EPA Methods 2 and 4 was performed to determine the flow

rate and moisture content of the stack gas.

2 Testing for Mercury and Non- Mercury Metallics were conduc ted over the course of two

days. One test run was conducted on the first day and the second and third test runs were

# L2010-275 

# 4 conducted on the second day.

3 During the Method 29 and OTM27/OTM 28 test s, EPA Methods 2 and 4 were performed

to determine the flow rate and mo isture content of the stack gas.

4 During the testing for semi-volatile orga nics and formaldehyde, EPA Methods 2 and 4

were performed to determine the flow rate and moisture content of the stack gas.

5 Methane was measured separately, in conj unction with THC meas urements utilizing

Method 25A.

6 SO2 testing wais required for both the “aci d gases” and “Non-Dioxin/Furan Organics”

test matrix.

1.3 TEST METHODS AND PARAMETERS

The sampling methods utilized to complete the test program are presented below:

40 CFR Part 60, Appendix A, EPA Methods

 Method 1 and 2 Volumetric Flow Rate Determination

 Method 3A/3B Oxygen and Carbon Dioxide

 Method 4 Moisture

 Method 6C Sulfur Dioxide

 Method 7E Oxides of Nitrogen

 Method 10 Carbon Monoxide

 Method 18 Methane

 Method 25A Volatile Organics

 Method 26A Hydrogen Chloride and Hydrogen Fluoride

 Method 29 Metals

 Method 30B Mercury

EPA Other/Conditional Test Methods (CTM)

 OTM 27 Particulate Matter

 OTM 28 Condensable Particulate Matter

 CTM-033 Hydrogen Cyanide

# L2010-275 

# 5 Test Methods for Evaluating Solid Wa ste, Physical/Chemical Methods (SW-846

Methods)

 Method 0010 Semi-Volatile Organics/POM

 Method 0011 Formaldehyde

 Method 0031 Volatile Organics

1.4 PROCESS MONITORING

Dominion personnel were responsible for the documentation of facility operating conditions

during the test program. Plan t operating data collected by Dominion plant personnel has been

included in the Final Report. The followi ng data were recorded during each test run.

 Coal Firing Rate (tons/hr)

 Average Heat Input (MMBtu/hr)

 Steam Output (k-lb steam-hr)

 Facility CEMS data for O 2 

# and CO 2 

# (percent)

 Stack Flow (DSCFM)

 Flue Gas Temperature (degrees F)

 Net Electrical Generation (MWh)

 Gross Electrical Generation (MWe)

 Pressure Drop Across FGD (inches H2O)

1.5 FUEL SAMPLING

As-fired coal samples were collected by f acility personnel during each metals, mercury,

particulate matter, acid gas, and dioxin/furan te st run. At least three samples of the fuel

combusted were collected, composited, and submitted for analyses. The samples were prepared

for analyses in accordance with ASTM D2013-09. An alyses of the samples are detailed in Table

1-2.

# L2010-275 

# 6 TABLE 1-2. LIST OF ANALYTICAL METHODS FOR FUEL ANALYSES

Analyte Method Units

Higher Heating Value ASTM D 2015 Btu/lb

Moisture ASTM D 3173 %

Mercury EPA 7473 ppm

Total Selected Metals SW 846 6010B 1 

# , SW 846 7060A 2



# , SW 846 7041 3 

# , SW 846 7740 4



# , ASTM D 4208 5 

# , ASTM D 3761 6 

# ppm

1 For beryllium, cadmium, cobalt, ch romium, lead, manganese, and nickel.

2 For arsenic

3 For antimony

4 For selenium

5 For chlorine

6 For fluorine

# L2010-275 

# 7 2.0 SUMMARY OF RESULTS

Testing for the U.S. EPA Utility MACT ICR was conducted at Southampton, Unit 1 and Unit 2

Common Stack between April 26, 2010 and April 29, 2010. As presented in Table 1-1, sampling

for acid gases, mercury and non-metallics , and non dioxin/furans was performed.

2.1. ACID GASES

Testing for acid gases included: hydrochlori c acid (HCl), hydrogen fluoride (HF), hydrogen

cyanide (HCN), sulfur dioxide (SO2), and oxide s of nitrogen (NOx). Sampling for the acid

gases was conducted on April 29, 2010. The aver age emission rates are presented in Table 2-1.

TABLE 2-1. AVERAGE EMISSION RATES FOR ACID GASES FROM

UNIT 1 AND UNIT 2 COMMON STACK

POLLUTANT LB/MMBTU PPM @7% O2

HCl < 7.78E-05 NA

HF < 7.51E-05 NA

HCN 3.95E-03 NA

NOx 0.392 224.246

SO2 0.029 11.737

The detailed results for each test run are presented in Appendices B.1and B.5.

2.2 MERCURY AND NON-METALLIC HAPS

Testing for mercury (Hg) and non-mercury meta llic HAPs including metals, particulate matter

(PM 2.5 

# ), condensable particulate matter, was pe rformed between April 26 and April 27, 2010.

The average emission rates are presented in Table 2-2. Total filterable particulate was not

determined in conjunction with Method 29 sampling.

# L2010-275 

# 8 TABLE 2-2. AVERAGE EMISSION RATES FOR MERCURY AND

NON-METALLICS FROM

UNIT 1 AND UNIT 2 COMMON STACK

POLLUTANT LB/MMBTU

Hg 2.796E-07 (See Note)

Particulate Matter 1.19E-03

Condensible PM 3.07E-03

Antimony < 8.87E-08

Arsenic < 2.81E-08

Beryllium < 5.37E-08

Cadmium < 2.84E-08

Chromium 1.14E-06

Cobalt < 2.70E-07

Lead 6.90E-07

Manganese 1.10E-06

Nickel 1.80E-06

Selenium < 4.57E-07

The detailed results for each test run ar e presented in Appendices B.2, B.3, and B.4.

Note: The Method 30B for Hg specifies a spik e recovery of 85 – 115%. The three run spike

recovery determined for the test program wa s 119.8%. The high average is driven by the

recovery for run 2 that was determined to be 151.9%. Although the exact cause of the high

result cannot be determined from the sampling or anal ytical data, it is thought that this result is

most likely due to a discrepancy in the pre-spike amount on the A trap for this run. All other QA

criteria were achieved fo r this source and the paired run agreement is excellent, even for the run

that had the high spike recovery percentage (Run 2). Average sp ike recovery of the remaining

runs was 103.7%. Given all othe r indications are that the re sults are valid, the high spike

recovery from Run 2 was not used to invalidate the test results.

2.3 NON-DIOXIN FURANS

The sampling for non-dioxin/furan or ganics included: volatile orga nics, semi-volatile organics,

formaldehyde, total hydrocarbons (THC), methan e (CH4), carbon monoxide (CO), and sulfur

dioxide (SO2). Sampling was performed on April 28, 2010. The average emission rates are

presented in Table 2-3.

# L2010-275 

# 9 The detailed results for each test run are pr esented in Appendices B.5, B.6, B.7, B.8, and B.9

TABLE 2-3. AVERAGE EMISSION RA TES FOR NON-DIOXIN FURANS

POLLUTANT LB/MMBTU ug/DSCM @7% O2 PPM @7% O2

Volatile Organic

Compounds See Appendix B.8 See Appendix B.8 NA

Semi-Volatile

Organic Compounds See Appendix B.9 See Appendix B.9 NA

THC 6.14E-06 NA 0.004

CH4 3.57E-04 NA 0.585

Formaldehyde 1.94E-05 NA 1.72E-02

CO 0.035 NA 33.116

SO2 0.032 NA 13.080

# L2010-275 

# 10 3.0 FACILITY DESCRIPTION AND SAMPLING LOCATIONS

3.1 FACILITY DESCRIPTION

Southampton Power Station is located in Frank lin, Virginia. The station consists of a 63-

megawatt coal fired generating unit that is equipped with a fluidi zed gas desulfurization system

to reduce emissions of sulfur dioxide and ha s an exhaust gas baghouse to trap fly ash.

3.2 SAMPLING LOCATIONS

The exhaust effluent from Unit 1 and Unit 2 exits though a common stack. The internal diameter

of the exhaust stack is 8 feet (96 inches). Four ports, located on the sa me plane, are present on

the stack. Each sample port has a depth of 16 in ches. The sample ports are located 1056 inches

(equivalent to 11 stack diameters) upstream; and 1284 (equivalent to 13.4 stack diameters)

downstream from any disturbance.

TRC conducted a 24-point traverse for velocity and particulate matter sampling. Table 3-1

presents these traverse points. Each port was sampled at 6 points to achieve the total of 24

points.

TABLE 3-1. SAMPLING TRAVERSE POINTS FOR

UNIT 1 AND UNIT 2 COMMON STACK

Point Percent of Stack Diameter Distance From Wall (in.) Point Location (in.)

1 2.1 2.02 18.02

2 6.7 6.43 22.43

3 11.8 11.33 27.33

4 17.7 17.0 33.0

5 25.0 24.0 40.0

6 35.6 34.18 50.18

# L2010-275 

# 11 3.3 STRATIFICATION TEST FOR SO2, NOx, CO, O2 and CO2

To test for stratification, concen tration of the pollutant of inte rest was measured at twelve

traverse points located according to Tabl e 1–1 or Table 1–2 of Method 1. Samples were

collected for a minimum of twice the syst em response time at each traverse point.

The individual point and average pollutant concentr ations were calculated at each traverse point.

Provided the concentration at each point differs from the mean concentration for all traverse

points by no more than: (a) ± 5.0 pe rcent of the mean concentrati on; or (b) ± 0.5 ppm (whichever

is less restrictive), the gas stream was considered unstratified and samples were collected from a

single point that most closely matched the mean.

# L2010-275 

# 12 4.0 FIELD SAMPLING PROGRAM

4.1 OVERVIEW

This section describes the procedures that TRC followed during the field-sampling program.

Throughout the program TRC followed EPA Refe rence Methods per 40 CFR Part 60 Appendix

A, EPA Other Test Methods 27 and 28, EPA Conditional Test Method 033, and SW-846

Methods 0010, 0011, 0031. The remainder of this sect ion is divided into several subsections:

Field Program Description, Pr e-sampling Activities, and Onsite Sampling Activities.

4.2 FIELD PROGRAM DESCRIPTION

The test methods utilized in accordance with 40 CFR Part 60 were as follows:

 EPA Method 1 Sample Velocity Traverse for Stationary Sources

 EPA Method 2 Determination of Stack Gas Velocity and

Volumetric Flow Rate (Type S Pitot tube)

 EPA Method 3A Determination of Oxygen and Carbon Dioxide

Concentrations in Emissions from Stationary

Sources (Instrumental Analyzer Procedure)

 EPA Method 3B Gas Analysis for the Determination of Emission

Rate Correction Factor or Excess Air

 EPA Method 4 Determination of Moisture Content in Stack Gases

 EPA Method 6C Determination of Sulfur Dioxide Emissions from

Stationary Sources (Instrumental Analyzer

Procedure)

 EPA Method 7E Determination of Nitrogen Oxides Emissions from

Stationary Sources (Instrumental Analyzer

Procedure)

 EPA Method 10 Determination of Carbon Monoxide Emissions from

Stationary Sources (Instrumental Analyzer

Procedure)

# L2010-275 

# 13  EPA Method 18 Measurement of Gaseous Organic Compound

Emissions by Gas Chromatography

 EPA Method 25A Determination of Total Gaseous Organic

Concentration using a Flame Ionization Analyzer

 EPA Method 26A Determination of Hydrogen Halide and Halogen

Emissions from Stationary Sources, Isokinetic

Method

 EPA Method 29 Determination of Metals Emissions from Stationary

Sources

 EPA Method 30B Determination of Total Vapor Phase Mercury

Emissions from Coal-Fired Combustion Sources

Using Carbon Sorbent Traps

The EPA Other/Conditional Test Met hods utilized were as follows:

 OTM 27 Determination of PM 10 

# and PM 2.5 

# Emissions from

Stationary Sources (Constant Sampling Rate

Procedure)

 OTM 28 Determination of Conde nsible Particulate Emissions

from Stationary Sources

 CTM-033 Sampling and Analysis for Hydrogen Cyanide

Emissions from Stationary Sources

The SW-846 test methods utilized were as follows:

 Method 0010 Sampling Method for Semi-Volatile Organic

Compounds and Products of Incomplete

Combustion Including Polycyclic Aromatic

Hydrocarbons (PAHs*)

*For the ICR, these are referred to as POM



#  Method 0011 Sampling for Selected Aldehyde and Ketone

Emissions from Stationary Sources

 Method 0031 Sampling Method fo r Volatile Organic Compounds

# L2010-275 

# 14 4.3 PRE-SAMPLING ACTIVITIES

Pre-sampling activities included equipment ca libration, pre-cleaning of the sample train

glassware, and other miscellaneous tasks. Each of these activities is described or referenced in

the following subsections. Other pre-sampling activities included team meetings, equipment

packing, and finalization of all details leading up to the coordi nated initiation of the sampling

program.

4.3.1 Equipment Calibration

Inspection and calibration of the equipment is a crucial st ep in ensuring the successful

completion of the field effort. All equipment was inspected for proper operation and durability

prior to calibration. Calibra tion of the following equipment was conducted in accordance with

the procedures outlined in EPA documents entitled " Quality Assurance Handbook for Air

Pollution Measurement Systems; Volume III - Stationary Source Specific Methods " and 40 CFR

Part 60 Appendix A. Copies of the equipmen t calibration forms can be found in Appendix E.

All calibrations were performed prior to the test program and included in the final report.

 Probe Nozzles (QA Handbook, Vol III, Section 3.4.2, pp. 19) - averaged three

internal diameter measurements of th e nozzle; difference between high and low

 0.1 mm. Recalibrate, reshape and sharpe n when nozzle becomes nicked, dented

or corroded.

 Pitot tubes (QA Handbook Vol III, S ection 3.1.2, pp. 1-13) - measured for

appropriate spacing and dimensions or cal ibrated in a wind tunnel. Rejection

criteria is given on the calibration sheet. A post-test check inspected for damage.

 Thermocouples (QA Handbook, Vol III, Section 3.4.2, pp. 12-18) – verified

against a mercury-in-glass thermometer at three points including the anticipated

measurement range. Acceptance limits - impinger + 2oF; DGM + 5.4oF; stack +

1.5 percent of stack temperature.

 Dry gas meters (EPA 40 CFR Part 60, Me thod 5, Section 5.3) - calibrated against

a critical orifice. A cceptance criteria - pretest Y

i 

# = Y = + 0.02; post test Y = +

0.05 Y

i



# .

 Field barometer (QA Handbook, Vol III, Section 3.4.2, pp. 18-19) – compared

# L2010-275 

# 15 against a mercury-in-glass barometer or use Airport Station BP and correct for

elevation. Acceptance criteria -

 0.02 in. Hg; post-test check will be the same.

 Analytical balances (QA Handbook, Vol III, Section 3.4.2, pp. 19) – Acceptance

criteria - calibrate with Standard Class-S weights within

 0.5 mg of stated value.

Corrective action: Have manuf acturer recalibrate or adjust.

4.3.2 Glassware Preparation

The sample train glassware necessary for the Method OTM 27/OTM 28 sampling trains was

precleaned using an Alconox  soap and water wash. Deionized water was used for rinsing

followed by an acetone rinse. The glassware was then rinsed with methylene chloride. After

cleaning, the glassware was baked at 300 o 

# C for six hours. The gla ssware was sealed with

Parafilm 

.

The sample train glassware necessary for the EPA Method 26A/CTM 033 sampling train was

precleaned using an Alconox  

# soap and water wash. Deionized water was used for rinsing

followed by air-drying. A final acetone rinse of the glassware was done, followed by air-drying.

The glassware was then sealed with Parafilm 



# .

The sample train glassware necessary for the EPA Method 29 sampling train was precleaned

using an Alconox  

# soap and water wash. Deionized water was used for rinsing followed by airdrying. The glassware was then soaked in nitric acid bath (10% nitric acid) followed again by a

deionized water rinse, a final acetone rinse, followed by air-drying. The glassware was then

sealed with Parafilm 



# .

The sample train glassware necessary fo r the SW-846 Method 0010 sampling train was

precleaned using an Alconox  

# soap and water wash. Deionized water was used for rinsing

followed by acetone rinses, methylene chloride rinses, followed by air-drying. The glassware

was then sealed with Teflon  

# tape or aluminum foil.

The sample train glassware necessary fo r the SW-846 Method 0031 sampling train was

# L2010-275 

# 16 precleaned using an Alconox  

# soap and water wash. Deionized water was used for rinsing

followed oven drying at 130 o 

# C for 2 hours. The glassware was then sealed with Teflon  

# tape or

aluminum foil.

4.3.3 Sample Media Preparation

All reagents were checked in accordance with the TRC’s existing QC Program to minimize the

probability of using contaminated solvents. This included the use of spectro-grade solvents from

the same lot and the collection and analysis of the appropriate blanks. All filters were desiccated

and weighed to the nearest 0.5 mg constant weight.

XAD-2 ® 

# resin used in the SW-846 Method 0010 (semi-volatile and total semivolatile/nonvolatile TOC) sampling trains was packed by the Field Sampling Subcontractor

laboratory(s) in specially desi gned sorbent traps. The XAD-2 ® 

# resin was purchased pre-cleaned

or prepared by the laboratory(s) to meet or exceed all quality control requirements specified in

SW-846 Method 0023A or SW-846 Method 0010, as applicable.

The SW-846 Method 0031 SMVOC traps were conditioned by the laboratory(s) in accordance

with procedures specified in SW-846 Method 0031. Laboratory preparation steps met or

exceeded all quality control requir ements specified in the method.

.

4.3.4 Continuous Emissions Monitoring

TRC conducted continuous emissions monitori ng for oxygen (EPA Method 3A), carbon dioxide

(EPA Method 3A), sulfur dioxide (EPA Method 6C), oxides of nitrogen (EPA Method 7E), and

carbon monoxide (EPA Method 10). TRC followed procedures outlin ed in the EPA Publication

340/1-83-016 regarding setup a nd operation of its Transpor table Continuous Emissions

Monitoring System (TCEMS).

The TCEMS consisted of three subsystems: sa mple acquisition/conditioning, sample analysis,

# L2010-275 

# 17 and a data acquisition system. Sample acqui sition/conditioning is designed to deliver a

representative sample of the gas stream to the sa mple analysis subsystem. Since the stream must

be clean and dry for O2, CO2, SO2, NOx, and CO analyzers, a glass fiber filter and noncontact

moisture condenser was used for particulate and moisture removal. The sample line was heat

traced to eliminate inline condensation prior to the condenser.

The data acquisition subsystem consisted of a dig ital data logger design ed to receive and log

instrument signals (raw voltages) at user-defin ed intervals. Once the system was set up, the

TCEMS was connected to a power source and br ought online. Sample line and signal wires

were strung between the sampling and TCEMS lo cations, and the probe was placed in the

sampling port at the sampling location.

Prior to insertion of the probe into the sampling location, the samp le/acquisition system was leak

checked by the following procedure:

a. plugged probe;

b. observed that flow in ro tometer reached zero Lpm;

c. observed vacuum; and

d. confirmed that sample vacuum during sampling did not exceed vacuum

attained during leak check.

The initial phase of instrumental analysis met hods requires calibration of all involved monitors.

At the beginning of each day, system instrument calibrations for zero and upscale gases were

performed prior to initiat ion of testing by system calibration gas injection. System calibrations

were performed both prior to and followi ng each run using a zero and one upscale gas

concentration. This was accomplished by directing calibration gas through the sample line and

conditioning system to assess system bias. Fo llowing completion of the required runs, final

system calibrations were performed. These proce dures allowed for determination of initial and

final system calibration error, as well as syst em drift. Typical ca libration gas values and

instrument range settings are listed in Table 4-1.

Calibration gases were EPA Protocol 1, traceable to the National Institute of Standards and

# L2010-275 

# 18 Technology (NIST). The measurement system perf ormance specifications as stated in 40 CFR

60 Appendix A, for Methods 3A, 6C, 7E, and 10 are listed in Table 4-2 and were the

performance criteria for this program.

TABLE 4-1. CALIBRATION GAS VALUES AND INSTRUMENT RANGES FOR

METHODS 3A, 6C, 7E, AND 10

Analyzer Range Conc. High Mid Zero

NO

x 

# 0 – 500 ppm 475 250 Nitrogen

SO 2 

# 0 – 100 ppm 90 50 Nitrogen

CO 0 - 200 ppm 180 90 Nitrogen

CO 2 

# 0 – 20 % 18 10 Nitrogen

O 2 

# 0 – 25 % 22 10 Nitrogen

TABLE 4-2. CEMS PERFORMANCE CRITERIA

Performance Criteria

Procedure O 2 

# /CO 2



# M3A SO 2



# M6C NO

x 

# M7E CO

M10

Zero Drift, % of range < ± 3 < ± 3 < ± 3 < ± 3

Calibration Drift, % of range < ± 3 < ± 3 < ± 3 < ± 3

Response time, seconds 60 60 60 60

Interference Response, % of

range < ± 2 < ± 2 < ± 2 < ± 2

NO2 to NO Converter, %

efficiency NA NA > 98 NA

Calibration Error, % of cal gas < ± 2 < ± 2 < ± 2 < ± 2



# 4.3.5 Interference Gas Test

Before mobilizing for the field portion of this program, the NO

x 

# analyzer was checked for

# L2010-275 

# 19 interference using the following gases:

Gas Concentration

Carbon monoxide 500 ± 50 ppm

Oxygen 20.9 ± 1 percent

Carbon Dioxide 10 ± 1 percent

Sulfur Dioxide 100 ± 10 ppm

Corrections to the measurement system or analyz er were made if the performance specifications

were not met.

4.3.6 Determination of CEMS Response Time

After the CEMS was set up, response time was de termined. Zero gas was introduced at the

CEMS calibration gas valve assembly until a stable zero response was achieved. Once achieved,

the calibration gas valve at the probe was switched to the effluent. Time of the response to a

stable effluent response was recorded. This upscale response was conducted one time. A

downscale response time was also conducted one tim e starting at a high span calibration value

and switching to the effluent.

4.3.7 NO 2 

# to NO Conversion Efficiency

At the start and at the completion of testing of each unit, the NO 2 

# to NO converter was checked

in accordance with the procedures of section 8.2.4 of EPA Method 7E.

4.4 ONSITE SAMPLING ACTIVITIES

Onsite sampling activities incl uded conducting velocity traverses, moisture measurements,

sampling for acid gases (HCl, HF, HCN, SO2 and NOx); mercury and non-mercury metallics

(metals, PM2.5 and CPM), non-dioxin/furan organics (volatile and semi-volatile organics,

# L2010-275 

# 20 formaldehyde, total hydrocarbons, methane, and car bon monoxide). Oxygen and carbon dioxide

measurements were also made.

4.4.1 EPA Methods 1 and 2 for Velocity Measurements/Cyclonic Flow

Velocity traverses were conducted on the outle t stack with an S-type pitot assembly in

accordance with EPA Reference Methods 1 and 2. An S-type pitot tube with an attached

inclined manometer was used to measure the ex haust velocities at th e sampling location. An

attached Type-K thermocouple with remote digita l display was used to determine the flue gas

temperature. During the test program, velocity measurements were c onducted during each test

run while operating the EPA Methods 23, 26A /CTM 033, 29, OTM 27/OTM28, sampling train.

The required number of velocity measurem ents points for each sampling location was

determined following EPA Method 1.

Cyclonic flow checks were conducted in accordan ce with Section 2.4 of EPA Method 1. This

procedure is referred to as the nulling technique. An S-type pitot tube connected to an inclined

manometer was used in this method. The Pitot t ube was positioned at each traverse point so that

the face openings of the P itot tube were perpendicular to the stack cross-sectional plane. This

position is called the “0  reference”. The velocity pressure (  P) measurement is noted. If the  P

reading was zero, the cyclonic angle was recorded as 0  . If the  P reading was not zero, the

Pitot tube was rotated clockwise or counter-clockwise until the  P reading became zero. This

angle was then measured with a leveled protractor and reported to the near est degree. After this

null technique was applied at each traverse po int, the average of the cyclonic angles was

calculated. If this average was less than 20  , the flow condition wa s acceptable to test.

4.4.2 EPA Method 3A/3B for O2/CO2

Oxygen and carbon dioxide concentrations were determined at the sampling location for each

test run in conjunction with a de signated sampling train in accordance with either EPA Method

3A “Determination of Oxygen and Carbon Dioxide C oncentrations in Emissions from Stationary

# L2010-275 

# 21 Sources (Instrumental Analyzer Procedure)” , or EPA Method 3B, " Gas Analysis for the

Determination of Emission Rate Correction Factor or Excess Air”.

For Method 3A, the oxygen and carbon dioxide c oncentrations were determined during the

continuous emissions monitoring described in Section 4.4.5 of this test report.

For Method 3B, an integrated sample was collect ed in a Tedlar bag during each test run. The

sample gas was drawn through a stai nless steel probe and through Teflon  

# sampling line

followed by a glass condenser unit to remove ex cess moisture which would interfere with the

operation of the pump and flow meter. Approxima tely 20 liters of sample gas were collected

during each test run. Following completion of the test run, a sa mple from the Tedlar bag was

drawn into the Orsat analyzer and immediately analyzed for percent CO 2 

# and percent O 2



# .

The O2/CO2 concentrations were needed to calculate the flue gas molecular weight for

determining volumetric flow rate as well as pr oviding the oxygen concen tration for correcting

applicable emission rates to 7% O2.

4.4.3 EPA Method 4 for Moisture Determination

Moisture was determined for each test run according to EPA Reference Method 4,

" Determination of Moisture Content in Stack Gases ". The principle of this method is to remove

the moisture from the sample stream and determine moisture either volumetrically or

gravimetrically. Method 4 was used in conj unction with the acid gas sampling trains, semivolatile and formaldehyde tests, and the metals and particulate matte r sampling trains.

4.4.4 EPA OTM 27/OTM 28 for Filterable PM and CPM

Particulate matter less than 2.5 microns in diameter (PM 2.5 

# ) was determined according to EPA

Method OTM 27, “Determination of PM 10 

# and PM 2.5 

# Emissions from Stationary Sources

(Constant Sampling Rate Procedure)” dated August 11, 2008. Condensable particulate matter

# L2010-275 

# 22 (CPM) measurements were made in accordance with EPA Method OTM 28, “ Dry Impinger

Method for Determining Condensible Particulate Emissions from Stationary Sources” (dated

August 11, 2008). Measurements were perf ormed for three four-hour test runs.

The sampling train consisted of a pre-cutter nozzle, a series of in-stack sizing devices (cyclones),

an in-stack filter, a heated glass probe with a S- type Pitot tube attached, four chilled impingers, a

Teflon (CPM) filter, and a metering console. A sc hematic of the sampling train is presented in

Figure 4-1.

The particulate with an aerodynamic size of < 2.5 microns (PM 2.5 

# ) was collected using an

Anderson 280 Series cyclone followed by a 63 mm Whatman EPM2000 glass fiber filter. The

Anderson cyclone and 63 mm filter were pre-heat ed prior to sampling. The first two impingers

were empty and the third impinger contained 100 mL of HPLC Grade de ionized, distilled (DI)

water. The fourth contained silica gel. Ini tial weights for all impingers were determined

gravimetrically prior to each test run.

Prior to initiating each sampling test run, a leak check of the entire sampling train was performed

in accordance with Section 8.6.8 of the test me thod. All leak checks and leakage rates were

documented on the relevant field test data sheets. The acceptance criterion for the OTM

27/OTM 28 train was a leak rate of ≤ 0.02 acfm or 4 percent of the average sample flow during

the test run, whichever was less.

Sampling was isokinetic (80 to 120 pe rcent) with readings of flue gas parameters recorded at

every sampling point during the traverse.

A preliminary velocity traverse (twelve point s maximum) was performed to determine the

velocity head (  p) and gas temperature at each traverse point. Based on the flue gas parameters,

the appropriate flow rate (acfm) in to the nozzle was selected for the PM 10 

# and the PM 2.5 

# cuts.

The desired nozzle size was calculated; the nozzle closest to the desired size was selected from

the nozzles available, and the desired velocity into the selected nozzle was calculated. The

# L2010-275 

# 23 desired velocity into the actual nozzle and the measured flue gas velocity at each traverse point

were compared to verify that the isokinetic ratio was maintained betw een 80% and 120%. The

sampling rate remained constant for the durati on of the run while the sampling time at each

traverse point was adjusted proportionally to the velocity at that point to provide a velocity

weighted sample. The  p measured and recorded for each poi nt during the preliminary traverse

was used to calculate the individual sampling durations during the test runs.

At the completion of the test run, the sample head (combined cyclone/filter assembly) was

removed from the stack. When the probe was co ol, external surfaces near the cyclone nozzle

were wiped and the inlet to the cyclone was cap ped. The combined cyclone/filter sampling head

was removed from the probe and the outlet of the filter housing was capped.

A leak check of the probe and sample train wi thout the sample head (combined cyclone/filter

assembly) was performed before and after each sa mpling run. All leak checks and leakage rates

were documented on the relevant field test data sheets. The acceptance criterion for the OTM 27

train was a leak rate of ≤ 0.02 acfm or 4 percent of the averag e sample flow during the test run,

whichever was less.

Following the completion of each test run, the OTM 27/OTM 28 sampling train was transported

to a recovery area onsite. Recove ry involved the quantitative transf er of particles less than or

equal to 2.5 microns. The recovery sequence proceeded as follows:

● The volume of the liquid collected in th e impingers and silica trap was weighed

and the measurement recorded on the field sampling data sheets. The color of the

silica gel was also noted.

● The filter housing was disassembled and the filter was transferred to its original

petri dish. Any particulate matter and/or filter fiber that adhered to the filter

holder gasket or filter support screen was transferred to the Pe tri dish using a dry

nylon bristle brush and/or sharp-edged bl ade. The container was sealed with

Teflon  

# tape and labeled with the appropriate sample information.

 The cyclone I cup, internal su rfaces of the nozzle, and the internal surfaces of the

cyclone I, including the outside surface to the downcomer line were brush-rinsed

with acetone into an amber glass container with a Teflon  

# -lined cap. The rinse

# L2010-275 

# 24 procedure was performed three times afte r which the container was sealed, liquid

level marked, and container labeled.

● The solids from the cyclone cup IV, the ace tone rinses of the cyclone I turnaround

cup, the inside of the downcom er line and the internal su rfaces of the cyclone IV,

were placed into an amber glass container with a Teflon  

# -lined cap. The container

was sealed, the liquid level marked, and labeled.

● The exit tube of the cyclone IV cup, and the front half of th e filter holder were

rinsed with acetone and placed into an amber glass container with a Teflon  

# -lined

cap. The container was sealed, liq uid level marked, and labeled.

● The impinger contents were purged with nitrogen to remove dissolved sulfur

dioxide and afterwards, the impingers were weighed and the contents collected in

an amber glass container with a Teflon  

# -lined cap. The impingers were then

rinsed with deionized water and the rinsate added to the sample container. The

container was sealed, liquid level marked, and labeled

● The back-half of the filter holder, probe, impingers, and connecting glassware

were rinsed three times with methylene chloride (MeCl

2 

# ) into a separate amber

glass container with a Teflon  

# -lined cap.

● The OTM 28 filter housing was disassembled and the Teflon  

# filter was

transferred to its original petri dish. The containe r was sealed with Teflon  

# tape

and labeled with the appropriate sample information.

At the completion of the triplicate test runs , blank samples were collected as follows:

● 100 ml of the acetone was collected direc tly from the wash bottle and placed into

a glass container. The container was s ealed, liquid level marked, and labeled as

the Acetone Rinse Blank.

● 100 ml of the methylene chloride was colle cted directly from the wash bottle and

placed into a glass container. The cont ainer was sealed, liquid level marked, and

labeled as the Methylene Chloride Rinse Blank.

● An unused filter from the OTM 27 sample train and an unused Teflon  

# filter from

the OTM 28 sample train were placed into Petri dishes and sealed with Teflon 



# tape and labeled.

● All containers were checked to ensure proper sealing, proper labeling, and that all

liquid levels were marked.

● All samples were logged onto a chain-of-custody form.

# L2010-275 

# 25 The samples were analyzed in accordance with th e procedures presented in Section 5.1 of this

test report.

4.4.5 Continuous Emissions Monitoring for O 2 

# , CO 2 

# , SO 2 

# , NO

x 

# , and CO

Emission testing was conducted for oxygen (E PA Method 3A), carbon dioxide (EPA Method

3A), sulfur dioxide (EPA Method 6C), oxi des of nitrogen (EPA Method 7E), and carbon

monoxide (EPA Method 10) at the Unit 1 and Unit 2 common exhaust stack.

The CEMS sampling train started with a stainles s-steel sampling probe. The sample stream was

then drawn through a glass fiber filter, heated (248  F ± 25  F) Teflon  

# sample line, and a sample

conditioner to remove the moisture and particulat e from the gas stream. The sample was then

drawn through Teflon  

# tubing by a leak-free Teflon  

# double diaphragm pump to a stainless-steel

sample manifold with and atmos pheric by-pass rotometer. The O 2 

# , CO 2 

# , SO 2 

# , NO

x 

# , and CO

analyzers withdrew samples from this manifold.

All CEMS data were recorded as averages by a digital data logger design ed to receive and log

instrument signals. The results were expressed in ppmvd for SO 2 

# , NO

x 

# , and CO; and in percent

for O 2 

# and CO 2 

# . A schematic diagram of the TRC CEMs is provided in Figure 4-2.

4.4.6 EPA Method 18 for Methane

Methane measurements were performed in c onjunction with Method 25 A measurements for

THC. Measurements were made using a Ther mo 55C Methane/Non-Methane analyzer which

utilizes gas chromatography and flame ionizatio n detection to separate methane from other

organics and report concentrations for both . TRC requested and r eceived approval for use of the

55C during the ICR via e-mail on March 04, 2010. Use of the 55C was previously Approved by

EPA under ALT066 for sources subject to 40CFR Part 60 Subpart JJJJJ.

# L2010-275 

# 26 4.4.7 EPA Method 25A for Methane and Total Hydrocarbons (THC)

Methane and Total Hydrocarbons (THC) emissions were measured in accordance with EPA

Method 25A, “ Determination of Total Gaseous Organic C oncentration using a Flame Ionization

Analyzer ”.

A TECO Model 55C was used to measure THC and CH 4 

# . This approach was preferable in that it

allowed for the direct measurement of THC.

The TECO Model 55C analyzer automatically and continuously monitors the THC

concentrations in a flowing gas mixture. The theory of operation is based on the principle of

flame ionization detection. In the flame ionizatio n detector, hydrogen is mixed with the sample

gas and is burned in a small jet. The ionizati on current in the hydrogen flame is measured. In a

pure hydrogen flame, very few ions are produced, but if an organic component or hydrocarbon is

burned in the flame, the ion current is greatly increased. The current provides a quantitative

measure of the amount of hydrocarbons in the flam e and is converted to a voltage output. The

hydrogen flame ionization detector is extremel y sensitive and is cap able of detecting

hydrocarbon levels in the low part per million range and is insensitive to inorganic gases such as

nitrogen, carbon dioxide, and water vapor. The inst rument utilizes a proprietary GC column to

separate the CH 4 

# prior to the direct analysis of THC.

All components of the sampling system that were in contact of the sample were either stainless

steel or Teflon  

# and were heated to a temperature of at least 250°F outside th e stack. A stainless

steel probe with a heated out-of-stack particulate filter, heated sample lines, and a heated sample

pump were used to deliver a representative sample of flue gas to the analyzer. The wet basis

concentration was converted to a dry basis using the calculated fl ue gas moisture value for each

run.

All THC and CH 4 

# data were recorded as averages by a digital data logger designed to receive

and log instrument signals. The results were measured in parts per million wet (ppm) for NMOC

# L2010-275 

# 27 and CH 4 

# . These results were converted to ppmd (using Method 4 data) to report ppmd values as

required by the ICR.

4.4.8 EPA Method 26A/CTM-033 for HCl/HF/HCN

Hydrogen Chloride and Hydrogen Fluoride (HCl/H F) emissions were determined according to

EPA Method 26A, " Determination of Hydrogen Halide and Halogen Emissions from Stationary

Sources, Isokinetic Method " (40 CFR Part 60 Appendix A). Hydrogen cyanide emissions were

determined according to EPA CTM 033, “Draft Method XHCN – Sampling and Analysis for

Hydrogen Cyanide Emissions from Stationary Sources.” EPA Method 26A was modified by

using the special sample collection options a nd analysis procedures of CTM-033 for the HCN

determination. Sampling consisted of three th ree-hour test runs at each outlet stack.

The sampling train consisted of a glass-lined he ated probe, with a glass button-hook nozzle. A

thermocouple and S-type pitot tube were attach ed to the probe for the measurement of gas

temperature and velocity. The sample gases passed through the probe assembly to a heated

glass fiber filter. The heated, glass-lined probe and filter holder were maintained at 248 o 

# F + 25 o 

# F

throughout all test runs. Downstr eam of the heated filter the samp le gas passed through a series

of eight ice-cooled impingers kept below 68  F to enable condensation of entrained moisture.

The first impinger served as a moisture knock-ou t. The next two impingers each contained 100

mL of 0.1N H 2 

# SO 4 

# . The fourth impinger was empty. Th e fifth, sixth, and seventh impingers

contained 100 mL of 10N sodium hydroxide (NaOH) solution (see note). The eighth impinger

contained a pre-weighed amount (200-300 g) of silica gel. The impingers were followed by a

dry gas meter, pump, and a calibrated orifice meter.

NOTE: It was essential that the NaOH impingers were maintained strongly basic (>PH 12)

throughout the sampling run. In utility boiler stack e nvironments; this requires measures such as

stronger base reagent, more reagent volume, or changing out the impinger contents during the

test run. The pH of the soluti on was monitored during each test using an indicator added to the

NaOH solution to ensure that the contents rema ined strongly basic th roughout the run.

# L2010-275 

# 28 Sampling was isokinetic and at a sampling rate of approximately 20 liters per minute. The

readings of flue gas parameters were recorded during the sampling period.

Leak checks of the entire Method 26A/CTM-033 sa mpling train were performed before and after

each sampling run. The acceptance criter ia was a post run leak rate of  0.02 cfm or  4% of the

average sampling rate (whichever was less) at the highest vacuum obtained during the test run.

Following the completion of each test run, the Method 26A/CTM-033 train was transported to

the recovery area onsite. The recove ry sequence proceeded as follows:

 Removed the sampling train to the recovery area.

● Noted the condition of the train (i.e., filter condition, impinger contents color,

silica gel color, etc.).

● If moisture was visible on the filter, connected the ambient air conditioning tube

at the probe inlet and operate the train w ith the filter heating system at least 248 o 

# F

at a low flow rate for a minimum of 30 minutes or until the filter was dry to

vaporize any liquid and haloge n halides on the filter to pull them through the train

and into the impingers.

 Measured the weights of the first seve n impingers and recorded the weight.

● Placed the contents of the first four impi ngers into a sample container (Container

#1). Rinsed the impingers, back-half of the filter holder and connecting glassware

with deionized water and added the rinse to Container #1. The container was then

sealed, labeled and the liquid level marked.

● Measured and recorded the pH of the contents of the fifth, sixth, and seventh

impingers. Placed the contents of the f ourth, fifth, and sixth impingers into a

sample container (Container #2). Rinsed the impingers and connecting glassware

with 0.1N sodium hydroxide and added the rinse to Container #2. The container

was then sealed, labeled and the liquid level marked.

 The silica gel impinger was weighed to obtain a final weight.

 All containers were checked to ensure proper sealing, proper labeling, and that all

liquid levels were marked. All sample s were logged onto a chain-of-custody

record.

# L2010-275 

# 29 The Method 26A train produ ced the following samples:

● Container No. 1 - Contents of Impinge rs 1, 2, and 3 (0.1N sulfuric acid impinger

catches)

● Container No. 2 - Contents of Impingers 5, 6 and 7 (10N sodium hydroxide

impinger catches)

Reagent blanks for the deionized water, the 0.1N H 2 

# SO 4 

# and the 10N NaOH were collected,

logged onto the chain of custody fo rm and submitted for analysis.

4.4.9 EPA Method 29 for Metals

Emissions of metals and particulate matter were determined in accordance with EPA Method 29

“Determination of Metals Emissions from Stationary Sources”.

The sampling train consisted of a heated gla ss-lined heated probe with a quartz button-hook

nozzle. A thermocouple and S-type pitot tube were attached to the probe for the measurement of

gas temperature and velocity. The sample gases passed through the probe assembly to a heated

glass fiber filter. The heated, glass-lined probe and filter holder were maintained at 248 o 

# F + 25 o 

# F

throughout all test runs. Downstr eam of the heated filter the samp le gas passed through a series

of ice-cooled impingers kept below 68  F to enable condensation of entrained moisture. The first

impinger was empty and served as a moisture knockout. The second and third impingers each

contained 100 mL of a 5% HNO 3 

# /10% H 2 

# O 2 

# solution. The fourth impinger was empty. The

fifth impinger contained between 200 and 400 grams of silica gel. No silicone grease was used

in the train. The impingers were weighed prior to assembling of the sample train. The impingers

were followed by a dry gas meter, leak free pum p, and calibrated orifice meter. A schematic

diagram of the sampling train is presented in Figure 4-3.

Sampling was isokinetic (  10%) with exhaust gas and train operating parameters recorded at

each sampling point.

# L2010-275 

# 30 Leak checks of the entire EPA Method 29 sampli ng train were performed before and after each

sampling run. All leak checks and leakage rates we re documented on the relevant field test data

sheets. The pre run l eak check criterion was  0.02 cfm at 15 in Hg. The acceptance criterion

was a post run leak rate of  0.02 cfm at the highest vacuum obtained during the test run.

Following the completion of each test run, th e EPA Method 29 train was transported to a

recovery area onsite. The sample recovery sequence was as follows:

 All openings on the sample probe, filter hol der and impingers were sealed with

Teflon ® 

# tape.

 The sampling train was removed to the recovery area.

 The condition of the train was noted (i.e., filter, impinger contents color, silica gel

color, etc.).

 Container No. 1 - Disassembled the filter housing and transferred the filter to its

original glass petri dish. Sealed the pe tri dish with Teflon ® 

# tape and labeled it with

the appropriate sample information. Any filter fibers adhering to the support gasket

were transferred to the petri dish.

 Container No. 2 - The front half of the train, nozzle, probe, and front-half filter

housing, cyclone and flask were brush-rinsed with 100 mL of 0.1N nitric acid into an

amber glass container with a Teflon ® 

# -lined cap. The container was sealed and

labeled.

 Container No. 3 - The contents of the first impinger and two 5% HNO 3 

# /10% H 2 

# O 2 

# impingers were weighed. The filter suppor t, back-half of the filter holder and

connecting glassware were rinsed three ti mes with a total of 100 mL of 0.1N HNO 3 

# into a glass amber container with a Teflon ® 

# lined cap. The impingers and connecting

glassware were rinsed with 0.1N HNO 3 

# . The container was sealed and labeled.

 Container No. 4 - The contents of the four th impinger were weighed and transferred

to a glass amber container with a Teflon ® 

# -lined cap. The impinger and U-tubes were

rinsed three times with a to tal of 100 mL portion of 0.1N nitric acid into a sample

container. The container was sealed and labeled.

 The silica gel impinger was weighed to obtain a final weight.

 All containers were checked to ensure proper sealing, proper labeling, and that all

liquid levels were marked. All samples we re logged onto a chain-of-custody record.

# L2010-275 

# 31 The EPA Method 29 train produced the following samples:

 Container No. 1 - Filter

 Container No. 2 - Front-Half 0.1N HNO 3 

# Rinse

 Container No. 3 - Impingers 1, 2, and 3 - 5% HNO 3 

# /10% H 2 

# O 2 

# Impingers Catch &

Rinse

 Container No. 4 - Impinger 4 - Impinger Catch & Rinse

4.4.10 EPA Method 30B for Mercury

The emissions of Mercury (Hg) were determined according to, " Determination of Total Vapor

Phase Mercury Emissions from Coal-Fired Combustion Sources Using Carbon Sorbent Traps ”

(40 CFR Part 60 Appendix A). Method 30B utili zed in-stack sorbent media coupled with

analysis of the integrated samples. Known vol umes of flue gas were extracted from a stack

through paired, in-stack, sorbent media traps at an appropriate nominal flow rate. Collection of

Hg on the sorbent media in the stack mitigated potential loss of Hg during transport through a

probe/sample line. The use of paired train sa mpling was utilized to determine measurement

precision and verify acceptability of the measured emissions data. The sampling criteria and

procedures of this Method have been shown to be appropriate for coal -fired utility boilers

(including units with post-combus tion emission controls), having va por-phase Hg concentrations

ranging from 0.1 μgm/dscm to 50 μgm/dscm.

The Method 30B sampling train consisted of a probe , the paired sorbent traps, an umbilical line,

moisture removal components, an airtight sample pump, and a dry gas meter. Sampling data was

recorded electronically through the use of an au tomated data acquisition and handling system.

A schematic diagram of the sampling train is presented in Figure 4-4.

The monitoring system samples the stack gas at a constant rate flow rate. The sampling was a

batch process. Using the sample volume measur ed by the dry gas meter and the results of the

analyses of the sorbent traps, the average mercur y concentration in the stack gas for the sampling

period was determined in units of micrograms per dry standard cubic meter ( μ g/dscm). The

following is a general outline of the sample collection procedure:

# L2010-275 

# 32 1. Performed an initial leak check with the sorbent traps in pl ace. Drew a vacuum in each

sample train. Adjusted the vacuum in the sample train to 15" Hg. Using the dry gas

meter, determined leak rate. The leakage rate must not exceed 4 percent of the target

sampling rate. Once the leak check passed this criterion, carefully released the vacuum in

the sample train then sealed the sorbent trap inlet until the probe was ready for insertion

into the stack or duct.

2. Prior to placement of the probe into the stack, removed the plug from the end of each

sorbent trap and stored each plug in a clean sorbent trap st orage container. Removed the

stack or duct port cap and inse rted the probe(s). Secured th e probe(s) and ensured that no

leakage occurred between the duct and environment.

3. Recorded initial data including the sorbent trap ID, start time, starting dry gas meter

readings, initial temperatur es, set-points, and any othe r appropriate information.

4. Obtained and recorded any esse ntial operating data for the fac ility during the test period,

e.g. , the barometric pressure must be obtaine d for correcting sample volume to standard

conditions. At the end of the data collecti on period, recorded the final dry gas meter

reading and the final values of all other essential parameters.

5. When sampling was completed, turned off th e sample pump, remove the probe/sorbent

trap from the port and carefully re-plugged th e end of each sorbent tr ap. Performed a leak

check with the sorbent trap s in place, at the maximum vacuum reached during the

sampling period. Used the same general approa ch described for the initial leak check.

Recorded the leakage rate and vacuum. The leak age rate must not exceed 4 percent of the

average sampling rate for the data collection period. Following the leak check, carefully

released the vacuum in the sample train.

6. Recovered each sampled sorbent trap by re moving it from the probe, sealing both ends.

Wiped any deposited material from the outside of the sorbent trap. Placed the sorbent trap

into an appropriate sample storage container and stored/preserved in appropriate manner.

4.4.11 Method 0031 for Volatile Organics

SW-846 Method 0031, "Sampling Method for Volatile Organic Compounds” was utilized to

determine the emissions of Volatile Organic Compounds (SMVOC). The sampling train

consisted of TenaxTM and AnasorbTM-747 resin tube s for the collection a nd analysis of the

volatile PICs during each test run. In addition, the 30 largest tentatively identified compounds

(TICs) for which the peaks are greater than 10% of the nearest internal standard were identified

and emission rates quantified.

The sampling system was a non-isokinetic sampli ng train using a glass-lined probe heated to

# L2010-275 

# 33 130 o 

# C ±5 o 

# C and flow rates which were predetermined ba sed on desired run times. Twenty liters

were collected through each set of traps at a flow rate of 1.0 liters per minute for twenty minutes.

Four sets of traps were used for each test run. Half of the tube se ts were collected during the first

half of the test run and the remaining half were collected durin g the second half of the test run.

The condensate was collected at the end of the run or when th e traps were changed and the

moisture knockout impinger was nearly full. A diagram of the sampling train is presented in

Figure 4-5.

The SMVOC was leak checked from the probe to the sampling pump before the first tube set

was collected (prior to the probe being placed in the exhaust duct) and afte r collection of the last

tube set (after the probe was removed from th e exhaust duct). All ot her leak checks were

conducted while the probe was in the exhaust duc t by isolating the sampling system between the

three-way valve just downstream of the pr obe and the sampling pump. A leak check was

performed before and after sampling with each tube set. All leak checks and leakage rates were

documented on the relevant field test data shee ts. The acceptance criteria for the SMVOC was a

leak rate of less than 0.1 inches of mercury ( 2.5 millimeters of mercury) as indicated on the

vacuum gauge after one minute at a vacuum that is above normal operating pressure for the

initial leak check and at least at the highest vacuum encountered during the run for the final leak

check.

SW-846 Method 0031 requires that two TenaxTM tubes and one AnasorbTM-747 tube be used in a

three-tube configuration of th e SMVOC. Four sets of SMVOC tubes were used during each

sampling run to collect the desire d sample amount (20 liters) per tube set. Tube sets were

analyzed by combined SW-846 Methods 5041A and 8260B. During the analysis, the two

TenaxTM tubes and one AnasorbTM-747 tube making up each set were analyzed separately so that

breakthrough and surrogate recovery from each tube type could be evaluated. For the three-tube

configuration, the TenaxTM tubes were coupled together as one sample, and the AnasorbTM-747

tube were analyzed separately.

One set of field blanks was collected during ea ch run. The SMVOC field blank sample tubes

were handled in the field in a manne r that is similar to that of th e sample tubes. The field blank

# L2010-275 

# 34 tubes were placed into the SMVOC, leak-checked , and removed from the train using the same

procedure as the actual samples. In additi on, one trip blank pair was packaged with each

shipment of samples to the laboratory. The aqueous SMVOC condensate from the SMVOC was

also analyzed for the same target analytes as the tube sets. Each shipment of condensate samples

were accompanied by a deionized water trip blank. As part of SW-846 Method 0031

requirements, the volatile content of the condensate was calculat ed by converting the

concentration of the analytes in the condensate to to tal analyte mass. The volatile mass of each

analyte was added to the analyte mass in the SMVOC resin tubes.

4.4.12 Method 0010 for Semi-Volatile Organics/POM

Semi-volatile organics/POM were sampled in accordance with SW-846 Method 0010. The

sampling train consisted of a heated, glass-lin ed probe, with a glass button-hook nozzle. A

thermocouple and S-type Pitot tube attached to an inclined manometer were attached to the probe

for measurement of gas temperature and velocity measurement. The sample gas passed through

the probe assembly to a heated glass fiber filter. The heated, glass-lined probe and filter holder

were maintained at 248°F ±25°F throughout each test period. (Note: A h eated transfer line of

appropriate length was used between the sampling pr obe and the heated glass fiber filter holder.

This heated transfer line was maintained within the same temperature range as the probe and

filter holder.) Downstream of the heater filte r, the gas passed through a water-cooled condenser

module, then through a sorbent module cont aining a minimum of 25 grams of XAD-2 ® 

# resin.

The XAD-2 ® 

# module was kept at a temperature below 68  F. The gas then passed through a

series of ice-cooled impingers kept below 68°F to enable condensation of entrained moisture.

The first impinger, acting as a condensate rese rvoir connected to the outlet of the XAD-2 ®



# module, was modified with a short stem in acco rdance with method requirements. The next two

impingers each contained 100 milliliters of deioni zed water. The fourth impinger was empty and

the fifth impinger contained a preweighed amount of silica gel. All connections within the train

were glass or Teflon ® 

# . No sealant greases were used. Th e impingers were followed by a dry gas

meter, pump, and calibrated orifice meter as presented in Figure 4-6.

One SW-846 Method 0010 semi-volatile and nonvolat ile total organics sample was collected for

# L2010-275 

# 35 each test run. Each sample was collected ove r a two-hour period. Sampling was isokinetic (±10

percent) with readings of exhaust gas paramete rs recorded at every sampling point during the

traverse. These readings include d the time, velocity, pressure, the target orifice pressure, the

actual orifice pressure, stack gas temperature, pr obe temperature, filter temperature, heated

transfer line temperature, sorbent trap temper ature, silica gel impinger temperature, dry gas

meter inlet and outlet temperatures, dry gas meter volume, and sample vacuum.

Leak checks of the entire sampling train were pe rformed before and after sampling in each of the

sampling ports. In the event any portion of th e train was disassembled and reassembled, leak

checks were performed prior to disassembling, and following reassembly of, the train. All leak

checks and leakage rates were documented on the re levant field test data sheet. The acceptance

criteria for the sampling train was a leak rate of  0.02 cubic feet per minute at a vacuum equal to

or greater than the maximum valu e reached during the sampling run.

Following the completion of each test r un, the SW-846 Method 0010 semi-volatile and

nonvolatile total organics train was leak checked a nd then transported to a recovery area onsite.

The sample recovery sequence proceeded as follows:

 

# Noted the condition of the train (i.e., filter condition, impinger contents color, silica gel

color, etc.).

 

# Disassembled the filter housing and transferred the filter to its original glass petri dish

with hexane-rinsed forceps. S ealed the container with Teflon ® 

# tape and labeled it with

the appropriate sample information.

 

# The front half of the train, probe nozzle, probe fitting, probe liner, heated transfer line,

and front-half filter housing were brush-rinsed with 1:1 methanol/methylene chloride into

the same amber glass co ntainer with a Teflon ® 

# -lined cap. The rinse procedure was

performed three times after which the contai ner was sealed and labeled. To prevent

contamination of the sample, all openings were sealed with Teflon ta pe just after sample

train disassembly and until rec overy was about to begin. In addition, nitrile gloves were

worn during all recovery proce dures and all recovery solvents were stored in appropriate

containers.

 

# The XAD-2 ® 

# resin sorbent module was tightly capped at both ends with Teflon ® 

# tape and

aluminum foil and labeled. The entire modul e was then covered with aluminum foil and

stored on-site on ice, or e quivalent, for transport to the laboratory for analysis.

# L2010-275 

# 36  

# The contents of the condensate knockout we re measured for volume to within ±1

milliliter using a graduated cylinder or by weighing to within ±0.5 grams using a triple

beam balance, or equivalent. The contents were transferred to a precleaned amber glass

container(s), sealed, and labele d, and stored on-site on ice, or equivalent, for transport to

the laboratory for analysis.

 

# All sampling train components located between the filter and the first wet impinger,

except the organic module, were rinsed with 1:1 methanol/methylen e chloride into the

same amber glass container with a Teflon ® 

# -lined cap. The rinse procedure was

performed three times after which th e container was sealed and labeled.

 

# The contents of the remaining three impingers were measured for volume to within ±0.5

milliliter using a graduated cylinder or by weighing to within ±0.5 grams using a triple

beam balance, or equivalent. The gain in weight or volume was used for moisture

calculations, analysis was not required.

 

# Silica gel (fourth impinger)- The color of the indicating silica gel was noted on the

recovery form to determine if it had been completely spent. The impinger was weighed

to within ±0.5 grams using a triple beam balan ce, or equivalent. The gain in weight was

used for moisture calculations. Analysis was not required.

 

# All sample containers were checked to ensure proper sealing, proper labeling, and that all

liquid levels were marked. All samples were then logged onto a chain-of-custody record.

The SW-846 Method 0010 semi-volatile and nonvolat ile total organics tr ain resulted in the

following samples:

 

# Filter

 

# XAD-2 ® 

# Module

 

# Front-Half Methanol/Methylene Chloride Rinse

 

# Condensate

 

# Back-Half Methanol/Methylene Chloride Rinse

4.4.13 Method 0011 for Formaldehyde

Formaldehyde was determined for each test run according to EPA Method 0011, “Sampling for

Selected Aldehyde and Ketone Em issions from Stationary Sources”

.

The sampling train consisted of a heated, glass- lined probe, with a glass button-hook nozzle. A

thermocouple and S-type Pitot tube were attach ed to the probe for the measurement of gas

# L2010-275 

# 37 temperature and velocity measurements. The sa mples gas passed through a series of five icecooled impingers kept below 68 o 

# F to enable condensation of entrained moisture. The first

impinger contained 200 ml of an aqueous acidi c 2,4-dinitrophenyl-hydraz ine (DNPH) solution;

the second and third impingers contained 100 mL of an aqueous acidic 2,4-dinitrophenylhydrazine (DNPH) solution . The fourth impinge r was empty and the fifth impinger contained a

preweighed amount of silica gel. The impingers were followed by a dry gas meter, pump, and

calibrated orifice meter. A schematic diagram of the sampling train is presented in Figure 4-7.

Sampling was isokinetic (± 10 percen t) with readings of flue gas parameters recorded at every

sampling point during the traverse.

Leak checks of the entire Method 0011 sampling train were performed before and after each

sampling run. In the event any portion of the train was disassembled and reassembled, leak

checks were performed prior to disassembling the train. All leak checks and leakage rates were

documented on the relevant field test data sh eet. The acceptance cr iteria for the Method 0011

train was a leak rate of  0.02 cfm at the highest vacuum obtained during the run.

Following the completion of each test run, the Me thod 0011 train was transported to a recovery

area onsite. The sample recovery sequence was as follows:

• Removed the sampling train to the recovery area;

• Noted the condition of the train (i.e., impinge r contents color, silica gel color, etc.);

• The front half of the train, nozzle and probe were brush-rinsed with methylene chloride

into an amber glass container with a Teflon R 

# -lined cap. The rinse procedure was

performed until no visible particles or yellow color.

• The contents of the first three impingers were measured for volume (or weight) and

transferred to the same glass amber container with a Teflon R 

# -lined cap. The impingers,

right angle, and U-tubes were rinsed three times with methylene chloride into the sample

container. Final rinses with methylene chlo ride and water were done. No more than 500

ml of methylene chloride were used for the recovery of the sample train. The container

was sealed and labeled (Container 1).

• The silica gel was returned to its original container and weighed to obtain a final weight.

• A volume of DNPH reagent and methylene chlo ride equal to the volume in Container 1

# L2010-275 

# 38 was transferred into a separate sample contai ner. The containers we re sealed and labeled

as the sample blank sample (Container 2).

• Transferred 200 ml of each washing solu tion (methylene chloride and water) into

separate sample containers. The containers were sealed and labeled as reagent blank

samples.

• All containers were checked to ensure pr oper sealing, proper labeli ng, and that all liquid

levels were marked. All samples were logged onto the chai n-of-custody record.

The EPA Method 0011 train resulted in the following sample:

• DNPH SampleL2010-27539Figure 4-1. Schematic ofOTM 27/OTM 028 Sampling Train

# L2010-275 

# 40 Figure 4-2. Schematic of TRC CEM System NO/NOx ANALYZER

SO2 ANALYZER

CO ANALYZER

O2 ANALYZER

CO2 ANALYZER

CHART RECORDER 1 CHART RECORDER 2

SAMPLING LINE

FILTER 3-WAY

VALVE



# DIAPHRAGM PUMP BYPASS VALVE SAMPLING PROBE 3-WAY

VALVE



# FILTER SPAN AND ZERO

GAS

CALIBRATION

GASES ZERO

AIR HIGH

RANGE

GAS MID

RANGE

GAS LOW

RANGE

GAS CONDENSER

DATA

LOGGER BYPASS VALVE

HEATED

SAMPLE

LINEL2010-27541Dry GasMeterVacuumLineVacuumGaugeBy-passValveAir-TightPumpOrificeSilicaGelTemperatureSensorMainValveGlass ProbeLinerManometerGlass ProbeTipHeated AreaGlass FilterHolderTemperatureSensorEmptyIceWaterBathEmpty(Optional)4% KMnO /10% H SO4425% HNO /10% H O322Figure 4-3. Schematic ofEPA Method 29 Sampling Train

# L2010-275 

# 42 Figure 4-4. Schematic of EP A Method 30B Sampling TrainL2010-27543L2010-27544Figure 4-6. Schematic ofSW-846 Method 0010 (Semi-Vol)L2010-27545Figure 4-7. Schematic ofSW-846 Method 0011 (HCOH)

# L2010-275 

# 46 5.0 ANALYTICAL PROCEDURE S AND CALCULATIONS

This section delineates the analytical procedures and calculations, which were used to analyze

and report the sample results for this test program.

5.1 ANALYTICAL PROCEDURES

5.1.1 Particulate Matter (PM2.5 and CPM)

Particulate matter (PM 2.5 

# ) analysis was accomplished by follow ing the procedures in EPA OTM

27, and OTM 28 and was conducted by TRC’s subcont ract laboratory, Resolution Analytics of

Sanford, North Carolina.

The dry filters, acetone rinses (pre-cutter/cyclone and front half rinses weighed separately) and

the acetones blank which represent the filterable pa rticulate were only analyzed according to the

procedures described in the methods.

The H2O (dry) impinger samples, back-half acetone/methylene chloride rinses, back-half CPM

(Teflon) filter, and solvent blanks which repr esent the condensable particulate matter were

analyzed according to the proced ures described in the method.

The condensable particulate matter samples coll ected utilizing EPA OTM 28 were analyzed in

accordance with Section 11 of the subject test method. Refer to Figure 5-1 which is a flowchart

outlining the steps to process and combine fracti ons from the CPM train. The sum of the organic

and inorganic fractions was reported as the total condensable particulate.

5.1.2 Metals

Analyses of the metals collected from the flue gas were accomplished by following the

procedures in EPA Method 29 and were conducted by a subcontr act laboratory.

# L2010-275 

# 47 5.1.3 Mercury

Analysis of each paired sorbent tube was c onducted by TRC’s subcontract laboratory, Ohio

Lumex Company of Twinsburg, Ohio. A M odel RA-915 fitted with the RP-M324 thermal

attachment was used to analyze each fraction of the charcoal tubes. The Ohio Lumex analyzer

was calibrated from 5 ng to 100 ng using NIST traceable standards. A 25 ng continuing

calibration verification (CCV) was prepared a nd analyzed following every ten analytical

samples. The charcoal tube was processed and the sorbent transferred onto a quartz ladle. The

ladle was inserted into the analyzer’s ther mo-catalytic conversion chamber (RP-M324) and

heated to ~ 680°C wherein mercury was convert ed from a bound state to the atomic state by

thermal decomposition in the two-section furnace. Mercury measurements take place in the

heated cell zone of the converter directly coupled to a spectrom eter. High temperature (~680oC)

and short residence time prevents mercury atoms from recombining with any “active” species

generated due to high temperature decomposition of the sample matrix. An external pump is

used to draw ambient air and purify it for combustion.

The RA-915 is also equipped with custom integr ation software that charts and records each

individual sample. This software integrates each sample peak providing the user with an area

count equivalent that is us ed to generate nanograms (ng) mercury per sample fraction.

The charcoal sorbent tube consisted of two fracti ons separated by a layer of glass wool. The first

section was the sample fraction. The second fr action was analyzed for breakthrough. The two

fractions from each tube were summed, and the total mercury analyzed was used to determine

concentration.

5.1.4 HCl/HF/HCN

Analyses of the Method 26A/CTM 033 samp les were conducted by TRC’s subcontract

laboratories. The masses of the HCl, HF a nd HCN in the samples were determined by ion

chromatography (IC).

# L2010-275 

# 48 5.1.5 Volatile and Semi-Volatile Organics

Analyses of the Method 0031 (Volatile) samples and the Method 0010 samples (SemiVolatile/POM) were conducted by a subcontract laboratory. Analysis of the samples were

performed in accordance with the specified methods by gas chromatography-mass spectrometry

(GC/MS).

5.1.6 Formaldehyde

Each EPA Method 0011 sample train yielded one i ndividual sample for analysis of formaldehyde

only. The samples were shipped to T RC’s sub-contract for analyses.

If there was any formaldehyde present, it r eacted with the DNPH solution to form the

formaldehyde dinitrophenylhydrazone derivative. The solution was extracted, solvent

exchanged, concentrated, and then analyzed according to the procedures specified in EPA

Method 0011 utilizing high performance liquid chromatography (HPLC).

# L2010-275 

# 49 Figure 5-1. OTM 28 Sample Processing Flow Chart

# L2010-275 

# 50 5.2 CALCULATIONS

5.2.1 Flow Rates

Calculations for the determination of dry gas samp led at standard conditions (dscf), gas velocity

at stack conditions (afpm), and gas volumetric flow rate at standard conditions (dscfm) were as

follows.

5.2.1.1 Volume of Dry Gas Sampled at Standard Conditions

Volume of dry gas sampled at standard conditions, dscf a



# dscf a 

# = 528  (Y)  (VM)  (PB + PM)

29.92  (TM + 460)

where:

a 

# = Dry standard cubic feet at 68  

# F (528  

# R) and 29.92 inches of Hg

Y = Dry gas meter calibration factor

VM = Sample gas Volume, ft 3



# PB = Barometric Pressure

PM = Average Orifice Pressure Drop, inches of Hg

TM = Average Dry Gas Temperature at meter,  

# F

5.2.1.2 Velocity of the Exhaust Gas

Stack gas velocity at stack conditions was de termined in terms of feet per minute(fpm)

fpm = 2/1

avg c



# MWPS 1 SDECp5130      

 

where:

c 

# = 5130 = 

#    

   minsec/60

OH in.R Hg in.mole- lb/lb

sec ft 85.5

2 

#       

 

# L2010-275 

# 51 Cp = Pitot tube coefficient

SDE

avg 

# = 

#   460 TempStack P

avg 

#  

avg



# PS = Stack Pressure, absolute

inches of Hg = Barometric Pressure ± Avg Stack Static Pressure

MW = Molecular Weight of Wet Stack Gas

5.2.1.3 Volumetric Flow Rate of the Exhaust Gas



# Stack gas volumetric flow rate at standard conditions, dscfm c



# dscfm c 

# = acfm  528  MD  PS

(29.92)  (TS

avg 

# + 460)

where:

c 

# = Dry standard cubic feet per minute at 68  

# F (528  

# R) and 29.92 in.Hg

acfm = Actual cubic feet per minute (f pm x cross sectional area of stack)

MD = Mole Fraction of Dry Gas (dimensionless)

PS = Stack Pressure, absolute, inches of Hg

TS

avg 

# = Average Stack Temperature

5.2.2 Particulate Matter - Grains per Dry Standard Cubic Foot



# Emission rates in terms of grains per dry standard cubic feet (gr/dscf) were calculated using the

PM weight in terms of milligrams (mg) divi ded by the volume of gas collected (dscf).

gr/dscf = 

#      

       

  

  

 

  460TM29.92 PMPBVMY528 mg(total) 0.0154

where:

mg (total) 

# = PM total 

# , filterable and condensable particulate

dscf = Dry standard cubic feet at 68  

# F (528  

# R) and 29.92 inches Hg

0.0154 = 0.0154 grains per milligram

Y = Dry gas meter calibration factor

VM = Volume metered, ft 3



# PB = Barometric Pressure, inches Hg

PM = Average Orifice Pressure Drop, inches Hg

TM = Average Dry Gas Temperature at Meter,  

# F

# L2010-275 

# 52 5.2.3 Particulate Matter – Pounds per Million BTU



# Emission rates were calculated in units of polluta nt mass per quantity of heat input (lbs/MMBtu).

The emission rates were calculated using the pa rticulate diluent concentrations and the fuelspecific F-factor derived from analysis of the fuel combusted and as specified in EPA

Method 19. Measured PM emission concentrations were conv erted to a mass emission factor in

terms of lbs/MMBtu using EPA Method 19, Equation 19-1:

PM total 

# (lbs/MMBtu) = PM total 

# (gr/dscf)  F d 

# (dscf/MMBtu)  ______20.9_____

7000 (gr/lb) 20.9 - % O 2 measured



# where:

F d 

# = Ratio of the volume of dry effluent gas to the gross calorific value of the

As-fired fuel. (The default F-factor for coal, 9780 dscf/MMBtu was used).

5.2.4 Vapor Phase Mercury Concentration



# Vapor Phase mercury mass emissions for each sampling period were calculated using the

average mercury concentration for that period, in conjunction with measur ements of the average

stack gas flow rate, corrected for the stack gas mo isture content. TRC utilized equation 30B-3 as

presented in 12.4 of the test method to determine concentration of mercury emitted during each

test period as follows:

C a,b 

# = (m 1 

# + m 2 

# )/ V

t



# Where:

C a,b 

# = Hg concentration for sample peri od, for sorbent trap “a” or “b” as

appropriate (ug/dscm).

m 1 

# = Mass of Hg measured on sorbent trap section 1 (ug)

m 2 

# = Mass of Hg measured on sorbent trap section 2 (ug)

V t 

# = Volume of gas sampled, (dscm)

# L2010-275 

# 53 The average concentration for the “a” and “b” tr aps was reported as the concentration for each

test run.

5.2.5 Mass of Hydrogen Halides HCl and HF



# The mass of the HCl and HF in the samples was calculated using the following equation:

M = K  Vs (Sx

- 

# - Bx - 

# )

Where:

M = Mass, ug

K = K HCl 

# is 1.028

K HF 

# is 1.053

V = Volume of filtered and diluted sample, ml

Sx - 

# = Analysis of sample of halide ion (Cl

- 

# or F - 

# ), ug/ml

Bx- = Mass concentration of solution blank for halide ion (Cl

- 

# or F - 

# ), ug/l

5.2.6 Total Weight of HCN in Sample



# The total weight of HCN in the samples was calculated using the following equation:

M = C  vol 

#  Vadj__

Valiq

Where:

M = Mass, ug

C = Concentration of HCN in sample, ug/L

 vol 

# = Total volume of recovered sample, mL

V adj 

# = Volume of sample aliquot after dilution

V aliq 

# = Volume of aliquot used

5.2.7 Concentrations of HCl, HF, and HCN



# The concentrations of HCl, HF, and HCN in the samples was calculated using the following

equation:

C = M  10 -3 

# mg/ug

Vm(std)

# L2010-275 

# 54 Where:

C = Concentration of HCl, HF, or HCN, mg/dscf

M = Mass of HCl, HF, or HCN, mg

Vm(std)= Dry Gas Volume Measured, Standard

5.2.8 HCl, HF, and HCN – Pounds per Million BTU



# Emission rates were calculated in units of pollutant mass per quantity of heat input (lbs/MMBtu).

The emission rates were calculated using the HC l, HF, and HCN concentrations and the fuelspecific F-factor derived from analysis of the fuel combusted and as specified in EPA

Method 19. Measured HCl, HF, and HCN emi ssion concentrations were converted to a mass

emission factor in terms of lbs/MMB tu using EPA Method 19, Equation 19-1:

(lbs/MMBtu) = ___HCl or HF (mg/dscf) _  F d 

# (dscf/MMBtu)  ______20.9_____

1 (lb)/453,590 (mg/lb) 20.9 - % O 2 measured



# where:

F d 

# = Ratio of the volume of dry effluent gas to the gross calorific value of the

As-fired fuel. (The default F-factor for coal, 9780 dscf/MMBtu was used).

5.2.9 Parts per Million Corrected to 7% Oxygen



# Concentrations in parts per million (ppm) we re corrected to 7% oxygen using the following

equation:

ppm @ 7% O 2 

# = ppm × ______(20.9 – 7)______

(20.9 - % O 2measured 

# )

5.2.10 Pounds per Million BTU



# Emission rates were calculated in units of polluta nt mass per quantity of heat input (lbs/MMBtu).

The emission rates were calculated using the po llutant concentrations and the fuel-specific F-

# L2010-275 

# 55 factor derived from analysis of the fuel combusted and as specified in EPA Method 19.

Measured pollutant concentrations were conve rted to a mass emission factor in terms of

lbs/MMBtu using EPA Method 19, Equation 19-1:

(lbs/MMBtu) = ____ (mg/dscf) ____  F d 

# (dscf/MMBtu)  ______20.9_____

1 (lb)/453,590 (mg/lb) 20.9 - % O 2 measured



# where:

F d 

# = Ratio of the volume of dry effluent gas to the gross calorific value of the

As-fired fuel. (The default F-factor for coal, 9780 dscf/MMBtu was used).

5.2.11 Formaldehyde

5.2.11.1 Total Formaldehyde



# Total formaldehyde (mg) was determined using the following equation:

CHOH (mg) = Cd × V × DF × {[g/mole aldehyde]  [g/mole DNPH derivative]}  10 -3 

# mg/ug

where:

Cd = measured concentration of DNPH-formaldehyde derivative, ug/mL

V = organic extract volume, mL

DF = dilution factor

5.2.11.2 Concentration



# The concentration of formaldehyde in the stack gas was determined suing the following

equation:

C f 

# = K [total formaldehyde, mg]

Vm(std)

where:

K = 35.31 cu.feet/cu.meter if Vm(std) is expressed in English units

# L2010-275 

# 56 = 1.00 cu.feet/cu.meter if Vm(std) is expressed in metric units

Vm(std)= volume of gas sample as measured by dry gas meter, corrected to standard

conditions, dscm

5.2.12 CO, SO 2 

# and NO

x 

# – Pounds per Million BTU



# Emission rates were calculated in units of polluta nt mass per quantity of heat input (lbs/MMBtu).

Pounds per million Btu were calculated using the pollutant and diluent concentrations and the

fuel-specific F-factor based up on the fuel combustion characteri stics and EPA Method 19. The

measured concentrations of CO, NO

x 

# and SO 2 

# in units of parts per million (ppm) were converted

to mass per unit volume (lbs/scf) for these calculations.

The conversion factors were:

NO

x 

# lbs/scf = ppm (vd) NO

x 

#  1.194  10 -7



# SO 2 

# lbs/scf = ppm (vd) SO

x 

#  1.66 × 10 -7



# CO lbs/scf = ppm (vd) CO  7.26× 10 -8



# Next, CO, NO

x 

# and SO 2 

# in terms of lbs/scf were converted to a mass emission rate in terms of

pounds per million Btu (lbs/MMBtu) as follows:

E = lbs/scf  F

d 

#  20.9_______

20.9% - O 2 measured



# where:

E = Mass emission rate of CO, NO

x 

# and SO 2 

# in terms of lbs/MMBtu.

F

d



# = Ratio of the volume of dry effluent gas to the gross calorific value of the

as-fired fuel. (The default F-factor for coal, 9780 dscf/MMBtu was used).

# L2010-275 

# 57 6.0 QUALITY ASSURANCE

6.1 OVERVIEW



# TRC Environmental Corporation management is fully committed to an effective Quality

Assurance/Quality Control Program whose objective is the delivery of a quality product. For

much of TRC's work, that product is data re sulting from field measurements, sampling and

analysis activities, engineering assessments, an d the analysis of gathered data for planning

purposes. The Quality Assurance Program works to provide complete, precise, accurate,

representative data in a timely manner for each project, considering both the project's needs and

budget constraints.

This section highlights the specific QA/QC procedures that were followed for this Test Program.

6.2 FIELD QUALITY CONTROL SUMMARY

6.2.1 Calibration Procedures



# Calibration of the field sampling equipment was pe rformed prior to the field sampling effort.

Copies of the calibration sheets were submitted to th e field team leader to take onsite and placed

into the project file. Calibrations were perf ormed as described in the EPA publications " Quality

Assurance Handbook for Air Pollution Measuremen t Systems; Volume III - Stationary Source

Specific Methods 

# " and EPA 40 CFR Part 60 Appendix A. Calibrations were performed as

described in Method 30B. Equipment to be calibrated included the sample metering systems,

nozzles, barometers, thermocouples, and Pitot tubes. All calibrations were available for review

during the test program. Copies of the exam ple equipment calibration forms are presented in

Appendix E.

6.2.2 Equipment Leak Checks



# Prior to sampling, each sampling train was leak checked according to the procedures outlined in

# L2010-275 

# 58 EPA OTM 27/OTM 28, Method 26A/CTM033, Met hod 29, and Method 30B. Final leak checks

were performed to ensure that no leaks develop in the train during the course of each test run.

All leakage rates, if any fo und, were recorded on the appr opriate field data sheet.

6.2.3 Calibration Gases



# All calibration gases used to conduct instrument calibrations were prepared in accordance with

the EPA Protocol 1.

6.2.4 Cyclonic Flow Check



# The absence of cyclonic flow was established pr ior to sampling, in accordance with Section 2.4

of EPA Method 1.

6.2.5 Method Blanks



# One Method blank for each of the sampling tr ains were collected dur ing the field-sampling

program to ensure sample quality. Blank correction of test results is not permitted under Method

30B and was not utilized.

6.2.6 Spike Recovery (for Method 30B)



# Method 30B requires demonstratio n that an average spike recove ry of 85%-115% is achieved

utilizing a minimum of three runs in order to valid ate analytical results. For this test program a

pre-spike amount was selected for section 1 of each spiked trap. The average spike recovery

values have been presented in the final report.

6.3 SAMPLE CHAIN OF CUSTODY



# Chain-of-custody of the samples were initiated and maintained as follows:

# L2010-275 

# 59 • Each sample that was collected was labeled, sealed, and the liquid level marked on

appropriate samples.

• Each sample was recorded on the chain-of-custody form.

• Custody of the samples was retained by TRC until delivery to the analytical laboratory

for analysis.

6.4 DATA REDUCTION, VALI DATION, AND REPORTING



# Specific QC measures were used to ensure the generation of reliable data from sampling and

analysis activities. Proper collection and orga nization of accurate inform ation followed by clear

and concise reporting of the data is a primary goal in all projects.

6.4.1 Field Data Reduction



# The Field Team Leader and at least one other fi eld crewmember reviewed the data collected in

the field. Any recording errors or discrepancies were noted on the field data sheet. The field

sampling data sheets are presented in Appendix A.

6.4.2 Laboratory Analysis Data Reduction



# Analytical results were reduced to concentration units specified by the analytical procedures,

using the equations provided in the analytical procedures.

6.4.3 Data Validation



# TRC supervisory and QC personnel use validation me thods and criteria appropriate to the type of

data and the purpose of the measurement. Reco rds of all data were maintained, including any

judged to be an "outlying" or s purious value. The persons who va lidated the data have sufficient

knowledge of the technical work to identify questionable values.

The Field Team Leader and/or the Field QC Coor dinator based on their re view of the adherence

to an approved sampling protocol and written sample collection procedure validated field-

# L2010-275 

# 60 sampling data.

Analytical data were validated using criteria outl ined below. TRC utilized results from the field

method blank to further validate analytical result s. Furthermore, TRC reviewed all laboratory

raw analytical data to verify th e calculated results presented.

The following criteria were used to evaluate the field sampling data:

• Use of approved test procedures;

• Proper operation of the process being tested;

• Use of properly operating and calibrated equipment;

• Leak checks conducted before and after tests;

• Use of reagents conforming to QC specified criteria;

• Proper chain-of-custody maintained.

The criteria listed below were used to evaluate the analytical data:

• Use of approved analytical procedures;

• Use of properly operating an d calibrated instrumentation;

• Results of Reagent and Method Blanks.

6.4.4 Data Reporting



# All data has been reported in standard units depending on the measurement and the ultimate use

of the data. The bulk of the data was comput er processed and reported using Excel as follows:

 Exhaust Gas Stream

- Gas Properties:

a. Moisture, dscf and percent by volume

b. Flow rate, dscfm and acfm

c. Pressure, inches of Hg

d. Temperature,  

# F

- Gas Diluents

a. O 2 

# , percent

b. CO 2 

# , percent

- SO 2 

# , and NO

x 

# :

a. ppmvd@7% O 2 

# , and lb/MMBtu

- THC, CH4, HCOH, and CO:

# L2010-275 

# 61 a. ppmvd@7% O 2 

# , and lb/MMBtu

- HCl, HF, and HCN:

a. lb/MMBtu

- Particulate:

a. lbs/MMBtu

- Hg:

a. lbs/MMBtu

- Metals:

a. lbs/MMBtu

- Volatile and Semi-Volatile Organics:

a. ug/dscm@7% O 2 

# , and lb/MMBtu

# L2010-275 

# APPENDIX A

FIELD SAMPLING DATA SHEETS

# L2010-275 

# APPENDIX A.1

CYLONIC FLOW CHECKS AND

PRELIMINARY FLOWS

# L2010-275 

# APPENDIX A.2

HCL, HF, AND HCN FIELD SAMPLING DATA

# TEST DATA SUMMARY

Client: Dominion

Location: Southhampton

Unit: Unit Common

Load/Condition: Normal

M26A/CTM033 Dates: 4/29/2010

Prelim. Run 1 Run 2 Run 3

Dates: 4/29/2010 4/29/2010 4/29/2010

Barometric Pressures: 30.25 30.25 30.25



# TABLE OF CONTENTS:

K-Factor Sheet - Run 1

K-Factor Sheet - Run 2

K-Factor Sheet - Run 3

Nozzles

Data Sheet

Run Sheet - Preliminaries

Run Sheet - Run 1

Run Sheet - Run 2

Run Sheet - Run 3

Calculation Sheet

Parameter Run 1 Run 2 Run 3 3-RUN AVG.

Total Sampling Time, Min. 180 180 180 180

Stack Gas Oxygen Content, O2% 6.7 6.7 6.5 6.6

Stack Gas Carbon Dioxide Content, CO2% 12.4 12.4 12.6 12.4

Gas Sample Volume at Standard Conditions, cu. ft. 174.593 176.261 170.685 173.846

cu. m. 4.943 4.990 4.832 4.922

Dry Stack Gas Flow Rate (Dry, STP), dscf/min 187,161.3 188,125.1 181,593.9 185,626.8

dscm/min 5,298.5 5,325.8 5,140.9 5,255.1



# TRC Environmental Corporation

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

Project Number 170096-0030 Sampling Data Summary

M26A-ctm033-South-U-common Runs 1-3.xlsTOC

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M26A/CTM033

Unit Common

Normal

Run No: Run 1

Date: 4/29/2010

METER BOX ID: 90801 Orifice Delta H@: 1.731 Y FACTOR: 0.9873

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 5.5 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 13.0 % by volume

Pbaro Bar. Pressure at Base of Stack 30.00 in. Hg

% H 2 

# 0 Assumed Moisture Content 10.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter DCIR-7/32"-11 0.218 inches

Delta H@ Orifice Calibration Factor 1.731 in. H 2 

# 0

Elevation Elevation of Sampling Location 0 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -0.3 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 30.00 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 29.98 in. Hg

Md Dry Molecular Weight 30.30 lb/lb*mole

Ms Wet Molecular Weight 29.07 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 70 80 90 100

200 1.58 1.61 1.64 1.67

205 1.57 1.60 1.63 1.66

210 1.56 1.59 1.62 1.65

215 1.55 1.58 1.61 1.63

220 1.54 1.56 1.59 1.62

225 1.52 1.55 1.58 1.61

230 1.51 1.54 1.57 1.60

235 1.50 1.53 1.56 1.59

240 1.49 1.52 1.55 1.58

245 1.48 1.51 1.54 1.57

250 1.47 1.50 1.53 1.55

255 1.46 1.49 1.52 1.54

260 1.45 1.48 1.51 1.53

265 1.44 1.47 1.50 1.52

270 1.43 1.46 1.48 1.51

275 1.42 1.45 1.47 1.50

280 1.41 1.44 1.46 1.49

285 1.40 1.43 1.45 1.48

290 1.39 1.42 1.45 1.47

295 1.38 1.41 1.44 1.46

300 1.37 1.40 1.43 1.45

305 1.37 1.39 1.42 1.44

310 1.36 1.38 1.41 1.43

315 1.35 1.37 1.40 1.42

320 1.34 1.36 1.39 1.41

321 1.34 1.36 1.39 1.41

Delta H = K factor * Delta P 

# M26A/CTM033

M26A-ctm033-South-U-common Runs 1-3.xls K-Fs R1 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M26A/CTM033

Unit Common

Normal

Run No: Run 2

Date: 4/29/2010

METER BOX ID: 90801 Orifice Delta H@: 1.731 Y FACTOR: 0.987

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 30.25 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.731 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 30.00 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 29.85 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 60 70 80 90

250 1.49 1.52 1.55 1.57

255 1.48 1.51 1.54 1.56

260 1.47 1.50 1.52 1.55

265 1.46 1.49 1.51 1.54

270 1.45 1.48 1.50 1.53

275 1.44 1.47 1.49 1.52

280 1.43 1.46 1.48 1.51

285 1.42 1.45 1.47 1.50

290 1.41 1.44 1.46 1.49

295 1.40 1.43 1.45 1.48

300 1.39 1.42 1.44 1.47

305 1.38 1.41 1.44 1.46

310 1.37 1.40 1.43 1.45

315 1.36 1.39 1.42 1.44

320 1.36 1.38 1.41 1.43

325 1.35 1.37 1.40 1.42

330 1.34 1.36 1.39 1.42

335 1.33 1.36 1.38 1.41

340 1.32 1.35 1.37 1.40

345 1.31 1.34 1.36 1.39

350 1.31 1.33 1.36 1.38

355 1.30 1.32 1.35 1.37

360 1.29 1.31 1.34 1.36

365 1.28 1.31 1.33 1.36

370 1.27 1.30 1.32 1.35

375 1.27 1.29 1.31 1.34

Delta H = K factor * Delta P 

# M26A/CTM033

M26A-ctm033-South-U-common Runs 1-3.xls K-Fs R2 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M26A/CTM033

Unit Common

Normal

Run No: Run 3

Date: 4/29/2010

METER BOX ID: 90801 Orifice Delta H@: 1.731 Y FACTOR: 0.987

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 30.25 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.731 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 30.00 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 29.85 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 55 65 75 85

270 1.43 1.46 1.49 1.52

275 1.42 1.45 1.48 1.51

280 1.41 1.44 1.47 1.50

285 1.41 1.43 1.46 1.49

290 1.40 1.42 1.45 1.48

295 1.39 1.41 1.44 1.47

300 1.38 1.40 1.43 1.46

305 1.37 1.40 1.42 1.45

310 1.36 1.39 1.41 1.44

315 1.35 1.38 1.40 1.43

320 1.34 1.37 1.39 1.42

325 1.33 1.36 1.39 1.41

330 1.33 1.35 1.38 1.40

335 1.32 1.34 1.37 1.39

340 1.31 1.33 1.36 1.38

345 1.30 1.33 1.35 1.38

350 1.29 1.32 1.34 1.37

355 1.28 1.31 1.33 1.36

360 1.28 1.30 1.33 1.35

365 1.27 1.29 1.32 1.34

370 1.26 1.29 1.31 1.33

375 1.25 1.28 1.30 1.33

380 1.25 1.27 1.29 1.32

385 1.24 1.26 1.29 1.31

390 1.23 1.26 1.28 1.30

395 1.22 1.25 1.27 1.30

Delta H = K factor * Delta P 

# M26A/CTM033

M26A-ctm033-South-U-common Runs 1-3.xls K-Fs R3 

# TRC Environmental Corporation

# NOZZLE SELECTION CALCULATIONS 

# M26A/CTM033

Unit Common

Normal

CHECK ALL INPUTS

Hand Input or Check Links

Input By:

Run 1 Run 2 Run 3

Date: 4/29/2010 4/29/2010 4/29/2010

Bar. Pressure, Pbar, in. Hg 30.25 30.25 30.25

Stack Temp.(F), ts (from prev. run) 125.0 192.3 193.3

Stack Temp. (R), Ts 585 652 653

Meter Temp. (F), tm 70.0 74.4 90.0

Meter Temp. (R), Tm 530 534 550

Pitot Number 0.0 0.0 0.0

Pitot Coefficient, cp 0.84 0.84 0.84

delta P avg. (from prev. run), dP, in. H2O 

# 0.94 2.03 2.03

O2 avg. (from prev. run), % 5.50 6.72 6.67

CO2 avg. (from prev. run), % 12.00 12.37 12.37

Static Pressure (from prev. run), in. H2O 

# -0.40 -0.98 -0.98

Ps, in. Hg 30.221 30.178 30.178

Mwd, lb/lb mole, dry 30.14 30.25 30.25

% Moisture (from prev. run) 13.0 14.5 13.9

MD 0.870 0.855 0.861

Mws, lb/lb mole, wet 28.562 28.473 28.548

delta H, (for sampling rate), in. H2O 1.731 1.731 1.731

delta H@, in. H2O 1.731 1.731 1.731

Qm, dscfm 0.750 0.750 0.750

Desired Nozzle , inches 0.225 0.192 0.189



# For Standard Test: dH = dH@, and therefore, Qm will be 0.75 dscfm.

For Different Sampling Rate: Input selected dH to yield desired sampling rate.

Desired Nozzle:

SQRT(SQRT((Ts*Mws)/(Ps*dP))*(0.0357*Qm*Pbar)/(Tm*cp*MD)) M26A/CTM033

M26A-ctm033-South-U-common Runs 1-3.xlsNozzles 

# TRC Environmental Corporation

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: 29-Apr-10

LOCATION: Southhampton PROJECT NO.: 170096-0030

UNIT: Unit Common PERSONNEL: TRC

CONDITION: Normal



# Data Input Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.



# M26A/CTM033

Parameter SYMBOL UNITS DATA Data

Test Number Prelim. Run 1 Run 2 Run 3

Test Date 1/0/1900 4/29/2010 4/29/2010 4/29/2010

Start Time 750 1127 1459

Stop Time 1107 1432 1812 3-RUN AVG.

Stack Diameter ds inches 318.00 96.00 96.00 96.00

Nozzle Diameter dn inches 0.218 0.218 0.218

Barometric Pressure Pbar in. Hg 30.25 30.25 30.25 30.25

Stack Static Pressure Pg in. H2O -0.98 -0.98 -0.98 -0.98

Pitot Coefficient cp none 0.84 0.84 0.84 0.84

Meter Calibration Factor Y none 0.9873 0.9873 0.9873

DH@ none 1.7310 1.7310 1.7310

Stack Gas Oxygen Content O2 % 6.7 6.7 6.5 6.6

Stack Gas Carbon Dioxide Content CO2 % 12.4 12.4 12.6 12.4

Net Moisture Gain (Impingers w/SiGel) Ww grams 627.8 602.0 709.5 646.4

Average Stack Temperature ts deg F 192.3 193.3 193.1 192.9

Average Meter Temperature tm deg F 81.4 81.3 86.3 83.0

Avg Delta H dH in. H2O 3.15 3.15 3.08 3.13

Average Square Root Delta H ASR dH in. H2O 1.771 1.772 1.752 1.765

Avg Velocity Head dP in. H2O 2.03 2.03 1.98 2.01

Average Square Root Delta P ASR dP in H2O 1.421 1.421 1.405 1.416

Gas Sample Volume Vm cu. ft. 177.986 179.664 175.596 177.749

Total Sampling Time min minutes 180 180 180

M26A-ctm033-South-U-common Runs 1-3.xls/Data 6/18/2010 8:27 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 29-Apr-10

LOCATION: Southhampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit Common

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 1 PAGE ONE OF ONE

Minutes per reading: 7.5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

A1 0.0 615.615 2.1 1.449 3.3 1.817 191 69 60

2 7.5 2.2 1.483 3.4 1.844 191 69 60

3 15.0 2.2 1.483 3.4 1.844 193 77 62

4 22.5 2.3 1.517 3.6 1.897 193 81 65

5 30.0 2.2 1.483 3.4 1.844 194 84 68

6 37.5 2.3 1.517 3.6 1.897 194 87 71

7 45.0 2.2 1.483 3.4 1.844 194 89 72

8 52.5 2.2 1.483 3.4 1.844 194 90 73

9 60.0 2.1 1.449 3.3 1.817 193 90 74

10 67.5 2.0 1.414 3.1 1.761 194 92 75

11 75.0 1.8 1.342 2.8 1.673 193 92 75

12 82.5 1.5 1.225 2.3 1.517 193 95 77

90.0 706.159

A1 90.0 706.411 1.8 1.342 2.8 1.673 184 84 78

2 97.5 1.6 1.265 2.5 1.581 193 94 79

3 105.0 2.1 1.449 3.3 1.817 193 97 81

4 112.5 2.1 1.449 3.3 1.817 193 95 80

5 120.0 2.2 1.483 3.4 1.844 193 93 79

6 127.5 2.2 1.483 3.4 1.844 193 95 80

7 135.0 2.1 1.449 3.3 1.817 193 94 80

8 142.5 2.1 1.449 3.3 1.817 191 88 79

9 150.0 2.0 1.414 3.1 1.761 191 90 78

10 157.5 1.9 1.378 2.9 1.703 191 92 78

11 165.0 1.7 1.304 2.6 1.612 191 93 79

12 172.5 1.7 1.304 2.6 1.612 191 94 80

180.0 793.853

Stop

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

180.0 177.986 2.025 1.421 3.15 1.771 192.3 81.4

Impinger Gain

impinger 1: 804.5 605.0 199.5 O2: 6.721 Start Time: 750

impinger 2: 916.0 763.0 153.0 CO2: 12.371 Stop Time: 1107

impinger 3: 763.0 697.0 66.0

impinger 4: 763.7 642.0 121.7 Static Pressure (Port A): -0.98 DIFF

PRESS. 

# M26A/CTM033 

# Field Data Run Sheets

M26A-ctm033-South-U-common Runs 1-3.xls/Run 1 6/18/2010 8:27 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 29-Apr-10

LOCATION: Southhampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit Common

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 2 PAGE ONE OF ONE

Minutes per reading: 7.5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

A1 0.0 794.102 1.9 1.378 2.90 1.703 191 81 77

2 7.5 2.0 1.414 3.10 1.761 192 80 76

3 15.0 2.1 1.449 3.30 1.817 193 87 75

4 22.5 2.2 1.483 3.40 1.844 193 89 76

5 30.0 1.9 1.378 2.90 1.703 193 93 77

6 37.5 2.2 1.483 3.40 1.844 194 88 77

7 45.0 2.3 1.517 3.60 1.897 194 87 76

8 52.5 2.3 1.517 3.60 1.897 194 87 75

9 60.0 2.1 1.449 3.30 1.817 194 91 76

10 67.5 2.0 1.414 3.10 1.761 193 86 74

11 75.0 1.7 1.304 2.60 1.612 193 87 75

12 82.5 1.4 1.183 2.20 1.483 193 88 75

90.0 883.460

A1 90.0 883.611 2.0 1.414 3.10 1.761 193 84 75

2 97.5 2.1 1.449 3.30 1.817 193 90 76

3 105.0 2.1 1.449 3.30 1.817 193 85 75

4 112.5 2.1 1.449 3.30 1.817 193 88 75

5 120.0 2.2 1.483 3.40 1.844 193 86 74

6 127.5 2.2 1.483 3.40 1.844 194 84 74

7 135.0 2.1 1.449 3.30 1.817 193 90 75

8 142.5 2.1 1.449 3.30 1.817 193 89 76

9 150.0 2.1 1.449 3.30 1.817 194 90 76

10 157.5 2.2 1.483 3.40 1.844 194 86 76

11 165.0 1.8 1.342 2.80 1.673 194 89 76

12 172.5 1.5 1.225 2.30 1.517 194 87 75

180.0 973.917

Stop

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

180.0 179.664 2.025 1.421 3.15 1.772 193.3 81.3

Impinger Gain

impinger 1: 858.0 616.0 242.0 O2: 6.673 Start Time: 1127

impinger 2: 840.0 702.0 138.0 CO2: 12.371 Stop Time: 1432

impinger 3: 786.0 736.5 49.5

impinger 4: 630.5 608.0 22.5 Static Pressure (Port A): -0.98

impinger 5: 810 0 779 0 31 0 Static Pressure (Port B): DIFF

PRESS. 

# M26A/CTM033 

# Field Data Run Sheets

M26A-ctm033-South-U-common Runs 1-3.xls/Run 2 6/18/2010 8:27 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 29-Apr-10

LOCATION: Southhampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit Common

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 3 PAGE ONE OF ONE

Minutes per reading: 7.5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

A1 0.0 975.197 2.1 1.449 3.30 1.817 194 81 75

2 7.5 2.1 1.449 3.30 1.817 194 87 75

3 15.0 2.2 1.483 3.40 1.844 194 89 76

4 22.5 2.2 1.483 3.40 1.844 193 93 78

5 30.0 2.2 1.483 3.40 1.844 193 93 78

6 37.5 2.2 1.483 3.40 1.844 194 91 78

7 45.0 2.2 1.483 3.40 1.844 193 89 78

8 52.5 2.1 1.449 3.30 1.817 193 95 80

9 60.0 2.0 1.414 3.10 1.761 193 93 80

10 67.5 1.9 1.378 2.90 1.703 193 92 79

11 75.0 1.8 1.342 2.80 1.673 192 98 80

12 82.5 1.4 1.183 2.20 1.483 192 97 82

90.0 1065.611

A1 90.0 1068.728 1.9 1.378 2.90 1.703 193 90 81

2 97.5 2.1 1.449 3.30 1.817 193 95 81

3 105.0 2.1 1.449 3.30 1.817 193 97 82

4 112.5 2.1 1.449 3.30 1.817 193 95 82

5 120.0 1.8 1.342 2.80 1.673 193 96 82

6 127.5 2.2 1.483 3.40 1.844 194 96 82

7 135.0 2.2 1.483 3.40 1.844 193 97 83

8 142.5 2.1 1.449 3.30 1.817 194 93 81

9 150.0 2.0 1.414 3.10 1.761 193 89 80

10 157.5 1.8 1.342 2.80 1.673 193 97 80

11 165.0 1.5 1.225 2.30 1.517 193 92 80

12 172.5 1.4 1.183 2.20 1.483 192 93 80

180.0 1153.910

Stop

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

180.0 175.596 1.983 1.405 3.08 1.752 193.1 86.3

Impinger Gain

impinger 1: 899.0 607.0 292.0 O2: 6.489 Start Time: 1459

impinger 2: 908.0 765.0 143.0 CO2: 12.570 Stop Time: 1812

impinger 3: 734.5 700.5 34.0

impinger 4: 661.0 649.0 12.0 Static Pressure (Port A): -0.98

impinger 5: 900.0 870.0 30.0 Static Pressure (Port B):

impinger 6: 785.5 765.5 20.0 Static Pressure (Avg.): -0.98

impinger 7: 779.5 757.0 22.5

impinger 5a: 750.5 741.0 9.5

Silica Gel imp: 1012.5 866.0 146.5

709.5 DIFF

PRESS. 

# M26A/CTM033 

# Field Data Run Sheets

M26A-ctm033-South-U-common Runs 1-3.xls/Run 3 6/18/2010 8:27 PM

# L2010-275 

# APPENDIX A.3

PARTICULATE FIELD SAMPLING DATAPM 10/2.5 SET-UP DATAPreliminary MeasurementsPlant NameSouthamptonSampling LocationCommon Stackdelta P Stack Temp.City/StateFranklin,VAin. H2Oo FNozzle Selection CalculationsD 11.501.2252151Duct Diameter, in.9621.801.3422152Width, in. (if rectangular)delta P low, in. H2O1.2031.801.3422153Duct Area,in27238delta P high, in. H2O2.10C 12.101.4492154Pitot Tube Coeffecient0.84Average dP, in H2O1.67421.801.3422155Meter Box ID90596Average tack Temp, o F215.031.201.0952156Meter Box Gamma (Y)0.997B 11.401.1832157Meter Box delta H@,in. H2O1.8321.801.3422158Estimated Meter Box Temperature, oF7531.801.3422159Barometric Pressure, in. Hg30.00A 11.801.34221510Flue Gas Static Pressure, in. H2O-0.8521.801.34221511Stack Pressure 30.0631.401.18321512Estimated % H2O10Desired Run Time, min330Number of Points12Base time per Point, min27.5Stack Gas O2, %5.5Stack Gas CO2, %13N2+CO81.5Dry Molecular Weight, lb/lb-mole30.30Wet Molecular Weight, lb/lb-mole29.07Dry Gas Mole Fraction0.900Viscocity of Stack Gas, micropoise 209.07Cyclone Flow Rate (Ideal), ft3/min0.504Cunningham Correction Factor1.09 2.25*Average:1.674 1.294 215.0Reynolds Number2698.5Lower Limit Cut for Cyc. I for Nre<316210.26Cut Diameter for Cyc. I - Middle of Overlap 10.63Lower Limit Cut for Cyc. I for Nre≥3162 10.63Velocity of Stack Gas81.663Calculated Nozzle Diameter0.137<--Ideal Nozzle DiameterVelocity of Gas in Nozzle20.2320.138<--Actual Nozzle DiameterNozzle #1 2 3 4 5 6 7 8 9 10 11Dn in.0.114 0.125 0.138 0.178 0.197 0.207 0.240 0.265 0.306 0.341 0.395<-- Input from Calibration SVn 118.597 98.642 80.933 48.646 39.715 35.970 26.758 21.948 16.460 13.255 9.878R min. 0.772 0.763 0.750 0.685 0.637 0.604 0.413 #NUM! #NUM! #NUM! #NUM!R max. 1.220 1.226 1.234 1.272 1.296 1.311 1.367 1.418 1.517 1.616 1.792Vmin. 91.59 75.28 60.68 33.34 25.28 21.71 13.38 #NUM! #NUM! #NUM! #NUM!Vmax 144.64 120.91 99.91 61.88 51.48 47.14 36.57 31.12 24.69 19.88 14.82Dp min.2.107 1.423 0.925 0.279 0.161 0.118 0.045 #NUM! #NUM! #NUM! #NUM!Dp max.5.254 3.671 2.506 0.962 0.666 0.558 0.336 0.243 0.153 0.099 0.055Sqrt dPFrom TraversePort Point

# Run I.D. PM2.5-10/OTM028-R1

Date 4/26/2010

Start 11:00

Finish 17:24

LA-2 Delta-P min 0.925 0.44

0.138 Delta-P max 2.506 0.38

Average delta-P 1.674 0.51

Barometric Pressure 30.05

Static Pressure -0.85

(min.) (min.) (ft 3 

# ) (in. H 2 

# O) (o F) (o F) (in. H 2 

# O)

1 

# 30.00 0.00 B-1 197.600 2.00 76 189 0.44

2 

# 31.50 30.00 2 208.971 2.2 79 187 0.44

3 

# 30.75 61.50 3 220.865 2.1 80 186 0.44

4 

# 30.75 92.25 4 232.512 2.1 81 186 0.44

5 

# 28.00 123.00 5 244.169 1.75 80 190 0.44

6 

# 28.00 151.00 6 254.810 1.75 79 189 0.44

7 

# 31.50 179.00 A-1 265.333 2.2 78 184 0.44

8 

# 32.75 210.50 2 278.060 2.4 76 190 0.44

9 

# 33.50 243.25 3 290.475 2.5 76 194 0.44

10 

# 31.50 276.75 4 302.956 2.2 78 194 0.44

11 

# 32.75 308.25 5 315.283 2.4 79 187 0.44

12 

# 28.50 341.00 6 328.330 1.8 78 189 0.44

13 

# end 369.50 339.457

14

15

16

17

18

19

20

21

22

23

24

25



# 369.5 141.857 2.110 78.3 188.8 0.44 delta H

delta H (Ts+50)

delta H (Ts-50)

Stack

Temp. Meter

Temp. Nozzle I.D.

Nozzle Diameter (in.)

DGM Reading City/State

Dwell

Time Elapsed

Time Point Southampton

Franklin,VA Plant Name

Sampling Location Common Stack

Time

Delta-H Delta-P

Average delta-H Total Run

Time Total Sample Volume (ft 3 

# ) Average

delta-P Average

Meter Temp Average

Stack Temp

# PM 10/2.5 SET-UP DATA

Preliminary Measurements

Plant Name Southampton

Sampling Location Common Stack delta P Stack Temp.

City/State Franklin,VA in. H 2 

# O o F



# Nozzle Selection Calculations D 1 2.00 1.414 189 1

Duct Diameter, in. 96 2 2.20 1.483 187 2

Width, in. (if rectangular) delta P low, in. H 2 

# O 1.75 3 2.10 1.449 186 3

Duct Area,in 2 

# 7238 delta P high, in. H 2 

# O 2.50 C 1 2.10 1.449 186 4

Pitot Tube Coeffecient 0.84 Average dP, in H 2 

# O 2.110 2 1.75 1.323 190 5

Meter Box ID 90596 Average tack Temp, o F 188.8 3 1.75 1.323 189 6

Meter Box Gamma (Y) 0.997 B 1 2.20 1.483 184 7

Meter Box delta H @ 

# , in. H 2 

# O 1.83 2 2.40 1.549 190 8

Estimated Meter Box Temperature, oF 75 3 2.50 1.581 194 9

Barometric Pressure, in. Hg 30.00 A 1 2.20 1.483 194 10

Flue Gas Static Pressure, in. H 2 

# O -0.85 2 2.40 1.549 187 11

Stack Pressure 30.06 3 1.80 1.342 189 12

Estimated % H 2 

# O 10

Desired Run Time, min 330

Number of Points 12

Base time per Point, min 27.5

Stack Gas O 2 

# , % 5.5

Stack Gas CO 2 

# , % 13

N 2 

# +CO 81.5

Dry Molecular Weight, lb/lb-mole 30.30

Wet Molecular Weight, lb/lb-mole 29.07

Dry Gas Mole Fraction 0.900

Viscocity of Stack Gas, micropoise 202.90

Cyclone Flow Rate (Ideal), ft 3 

# /min 0.482

Cunningham Correction Factor 1.08 2.25 *Average: 2.110 1.452 188.8

Reynolds Number 2762.3

Lower Limit Cut for Cyc. I for N

re 

# <3162 10.33

Cut Diameter for Cyc. I - Middle of Overla p 10.66

Lower Limit Cut for Cyc. I for Nre ≥ 3162 10.64

Velocity of Stack Gas 89.86541

Calculated Nozzle Diameter 0.128 <--Ideal Nozzle Diameter

Velocity of Gas in Nozzle 23.172 0.126 <--Actual Nozzle Diameter

Nozzle # 1 2 3 4 5 6 7 8 9 10 11

Dn in. 0.138 0.126 0.161 0.175 0.197 0.207 0.240 0.265 0.306 0.341 0.395 

# <-- Input from Calibration S

Vn 77.275 92.695 56.773 48.053 37.920 34.344 25.549 20.956 15.716 12.656 9.432

R min. 0.749 0.762 0.716 0.690 0.633 0.599 0.399 #NUM! #NUM! #NUM! #NUM!

R max. 1.235 1.227 1.255 1.270 1.298 1.312 1.369 1.421 1.521 1.622 1.800

Vmin. 57.87 70.59 40.67 33.14 24.01 20.59 12.77 #NUM! #NUM! #NUM! #NUM!

Vmax 95.43 113.72 71.24 61.01 49.21 45.07 34.98 29.78 23.57 18.98 14.15

Dp min. 0.875 1.302 0.432 0.287 0.151 0.111 0.043 #NUM! #NUM! #NUM! #NUM!

Dp max. 2.380 3.379 1.326 0.973 0.633 0.531 0.320 0.232 0.145 0.094 0.052 

# Port Point Sqrt dP

From Traverse

# Run I.D. PM2.5-10/OTM028-R2

Date 4/27/2010

Start 7:50

Finish 13:47

LA-1 Delta-P min 1.302 0.43

0.126 Delta-P max 3.379 0.37

A verage delta-P 2.110 0.51

Barometric Pressure 30.00

Static Pressure -0.85

(min.) (min.) (ft 3 

# ) (in. H 2 

# O) (o F) (o F) (in. H 2 

# O)

1 

# 26.50 0.00 A -1 339.800 1.95 59 188 0.43

2 

# 27.25 26.50 2 349.560 2.05 60 190 0.43

3 

# 27.50 53.75 3 359.458 2.1 61 191 0.43

4 

# 27.25 81.25 4 369.382 2.05 64 192 0.43

5 

# 26.50 108.50 5 379.340 1.95 65 192 0.43

6 

# 25.00 135.00 6 389.324 1.75 65 193 0.43

7 

# 26.50 160.00 B-1 398.150 1.95 66 181 0.43

8 

# 27.75 186.50 2 408.187 2.15 66 181 0.43

9 

# 27.75 214.25 3 418.400 2.15 66 185 0.43

10 

# 27.25 242.00 4 428.412 2.05 66 188 0.43

11 

# 26.75 269.25 5 438.539 2 67 188 0.43

12 

# 24.50 296.00 6 448.584 1.65 67 185 0.43

13 

# end 320.50 458.700

14 

# 457.457

15

16

17

18

19

20

21

22

23

24

25



# 320.5 118.900 1.981 64.3 187.8 0.43 Average

Stack Temp Average delta-H Total Run

Time Total Sample Volume (ft 3 

# ) Average delta

P Average

Meter Temp 

# City/State Franklin,VA

Delta-P Meter

Temp.

delta H (Ts-50) Nozzle I.D. delta H

Nozzle Diameter (in.) delta H (Ts+50) Time Plant Name Southampton

Sampling Location Common Stack

Stack

Temp. Delta-H Dwell

Time Elapsed

Time point DGM Reading

# PM 10/2.5 SET-UP DATA

Preliminary Measurements

Plant Name Southampton

Sampling Location Common Stack delta P Stack Temp.

City/State Franklin,VA in. H 2 

# O o F



# Nozzle Selection Calculations D 1 1.95 1.396 188 1

Duct Diameter, in. 96 2 2.05 1.432 190 2

Width, in. (if rectangular) delta P low, in. H 2 

# O 1.65 3 2.10 1.449 191 3

Duct Area,in 2 

# 7238 delta P high, in. H 2 

# O 2.15 C 1 2.05 1.432 192 4

Pitot Tube Coeffecient 0.84 Average dP, in H 2 

# O 1.981 2 1.95 1.396 192 5

Meter Box ID 90596 Average tack Temp, o F 187.8 3 1.75 1.323 193 6

Meter Box Gamma (Y) 0.9965 B 1 1.95 1.396 181 7

Meter Box delta H @ 

# , in. H 2 

# O 1.83 2 2.15 1.466 181 8

Estimated Meter Box Temperature, oF 80 3 2.15 1.466 185 9

Barometric Pressure, in. Hg 30.00 A 1 2.05 1.432 188 10

Flue Gas Static Pressure, in. H 2 

# O 7.5 2 2.00 1.414 188 11

Stack Pressure 29.45 3 1.65 1.285 185 12

Estimated % H 2 

# O 10

Desired Run Time, min 330

Number of Points 12

Base time per Point, min 27.5

Stack Gas O 2 

# , % 6.5

Stack Gas CO 2 

# , % 12.6

N 2 

# +CO 80.9

Dry Molecular Weight, lb/lb-mole 30.28

Wet Molecular Weight, lb/lb-mole 29.05

Dry Gas Mole Fraction 0.900

Viscocity of Stack Gas, micropoise 203.22

Cyclone Flow Rate (Ideal), ft 3 

# /min 0.486

Cunningham Correction Factor 1.08 2.25 *Average: 1.981 1.407 187.8

Reynolds Number 2730.1

Lower Limit Cut for Cyc. I for N

re 

# <3162 10.29

Cut Diameter for Cyc. I - Middle of Overla p 10.65

Lower Limit Cut for Cyc. I for Nre ≥ 3162 10.63

Velocity of Stack Gas 87.94859

Calculated Nozzle Diameter 0.130 <--Ideal Nozzle Diameter

Velocity of Gas in Nozzle 23.401 0.126 <--Actual Nozzle Diameter

Nozzle # 1 2 3 4 5 6 7 8 9 10 11

Dn in. 0.138 0.150 0.161 0.180 0.197 0.207 0.240 0.265 0.306 0.341 0.395 

# <-- Input from Calibration S

Vn 78.037 66.051 57.334 45.869 38.294 34.683 25.801 21.163 15.872 12.781 9.525

R min. 0.749 0.734 0.717 0.680 0.635 0.602 0.406 #NUM! #NUM! #NUM! #NUM!

R max. 1.235 1.244 1.254 1.275 1.297 1.311 1.368 1.419 1.519 1.619 1.796

Vmin. 58.48 48.48 41.11 31.18 24.32 20.86 12.90 #NUM! #NUM! #NUM! #NUM!

Vmax 96.35 82.19 71.92 58.48 49.67 45.49 35.29 30.04 23.81 19.17 14.29

Dp min. 0.876 0.602 0.433 0.249 0.151 0.111 0.043 #NUM! #NUM! #NUM! #NUM!

Dp max. 2.378 1.730 1.325 0.876 0.632 0.530 0.319 0.231 0.145 0.094 0.052 

# Port Point Sqrt dP

From Traverse

# Run I.D. PM2.5-10/OTM028-R3

Date 4/27/2010

Start 14:11

Finish 19:49

PM10-0.125 Delta-P min 1.303 0.44

0.126 Delta-P max 3.376 0.38

A verage delta-P 1.981 0.51

Barometric Pressure 29.25

Static Pressure -0.85

(min.) (min.) (ft 3 

# ) (in. H 2 

# O) (o F) (o F) (in. H 2 

# O)

1 

# 27.25 0.00 B1 457.700 1.95 63 181 0.44

2 

# 28.25 27.25 2 478.152 2.1 65 185 0.44

3 

# 28.25 55.50 3 488.365 2.1 58 186 0.44

4 

# 29.00 83.75 4 498.400 2.2 63 186 0.44

5 

# 27.50 112.75 5 498.860 2 66 186 0.44

6 

# 25.00 140.25 6 508.934 1.65 65 183 0.44

7 

# 26.50 165.25 A1 518.067 1.85 65 186 0.44

8 

# 28.50 191.75 2 527.897 2.15 68 187 0.44

9 

# 29.00 220.25 3 538.562 2.2 66 187 0.44

10 

# 30.00 249.25 4 549.296 2.35 70 187 0.44

11 

# 28.25 279.25 5 560.442 2.1 71 187 0.44

12 

# 25.00 307.50 6 570.728 1.65 71 180 0.44

13 

# end 332.50 580.039

14

15

16

17

18

19

20

21

22

23

24

25



# 332.5 122.339 2.019 65.9 185.1 0.44 Delta-H

Total Run

Time Total Sample Volume (ft 3 

# ) Average delta

P Average

Meter Temp Average

Stack Temp Average delta-H 

# Point DGM Reading City/State Franklin,VA Time

Nozzle I.D. delta H Plant Name Southampton

Sampling Location Common Stack

Nozzle Diameter (in.) delta H (Ts+50)

delta H (Ts-50)

Delta-P Meter

Temp. Stack

Temp. Dwell

Time Elapsed

Time

# L2010-275 

# APPENDIX A.4

METALS FIELD SAMPLING DATA

# TEST DATA SUMMARY

Client: Dominion

Location: Southampton

Unit: Unit 1 and 2

Load/Condition: Normal

M29 Dates:

Prelim. Run 1 Run 2 Run 3

Dates: 4/26/2010 4/27/2010 4/27/2010

Barometric Pressures: 29.07 29.13 29.13



# TABLE OF CONTENTS:

K-Factor Sheet - Run 1

K-Factor Sheet - Run 2

K-Factor Sheet - Run 3

Nozzles

Data Sheet

Run Sheet - Preliminaries

Run Sheet - Run 1

Run Sheet - Run 2

Run Sheet - Run 3

Calculation Sheet

Parameter Run 1 Run 2 Run 3 3-RUN AVG.

Total Sampling Time, Min. 240 240 240 240

Stack Gas Oxygen Content, O2% 6.545 6.067 5.995 6.202

Stack Gas Carbon Dioxide Content, CO2% 12.683 13.101 13.178 12.987

Gas Sample Volume at Standard Conditions, cu. ft. 232.253 220.990 224.365 225.869

cu. m. 6.575 6.256 6.352 6.394

Dry Stack Gas Flow Rate (Dry, STP), dscf/min 192,591.7 182,619.3 184,465.2 186,558.7

dscm/min 5,452.3 5,170.0 5,222.2 5,281.5



# TRC Environmental Corporation

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

Project Number 170096-0030 Sampling Data Summary

M29-South - U Common Runs 1-3.xlsTOC

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M29

Unit 1 and 2

Normal

Run No: Run 1

Date: 4/26/2010

METER BOX ID: 90596 Orifice Delta H@: 1.731 Y FACTOR: 0.9873

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 11.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.25 in. Hg

% H 2 

# 0 Assumed Moisture Content 13.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.731 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -0.4 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 29.00 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 28.97 in. Hg

Md Dry Molecular Weight 30.04 lb/lb*mole

Ms Wet Molecular Weight 28.47 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 80 90 100 110

180 1.57 1.60 1.63 1.66

185 1.56 1.59 1.62 1.65

190 1.55 1.58 1.61 1.63

195 1.54 1.56 1.59 1.62

200 1.52 1.55 1.58 1.61

205 1.51 1.54 1.57 1.60

210 1.50 1.53 1.56 1.59

215 1.49 1.52 1.55 1.57

220 1.48 1.51 1.53 1.56

225 1.47 1.50 1.52 1.55

230 1.46 1.49 1.51 1.54

235 1.45 1.47 1.50 1.53

240 1.44 1.46 1.49 1.52

245 1.43 1.45 1.48 1.51

250 1.42 1.44 1.47 1.50

255 1.41 1.43 1.46 1.49

260 1.40 1.42 1.45 1.48

265 1.39 1.41 1.44 1.46

270 1.38 1.40 1.43 1.45

275 1.37 1.39 1.42 1.44

280 1.36 1.38 1.41 1.44

285 1.35 1.38 1.40 1.43

290 1.34 1.37 1.39 1.42

295 1.33 1.36 1.38 1.41

300 1.32 1.35 1.37 1.40

301 1.32 1.35 1.37 1.40

Delta H = K factor * Delta P 

# M29

M29-South - U Common Runs 1-3.xls K-Fs R1 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M29

Unit 1 and 2

Normal

Run No: Run 2

Date: 4/27/2010

METER BOX ID: 90594 Orifice Delta H@: 1.842 Y FACTOR: 1.005

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.13 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.842 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 28.88 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 28.73 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 60 70 80 90

250 1.58 1.61 1.65 1.68

255 1.57 1.60 1.63 1.66

260 1.56 1.59 1.62 1.65

265 1.55 1.58 1.61 1.64

270 1.54 1.57 1.60 1.63

275 1.53 1.56 1.59 1.62

280 1.52 1.55 1.58 1.61

285 1.51 1.54 1.57 1.60

290 1.50 1.53 1.56 1.59

295 1.49 1.52 1.55 1.58

300 1.48 1.51 1.54 1.57

305 1.47 1.50 1.53 1.56

310 1.46 1.49 1.52 1.54

315 1.45 1.48 1.51 1.53

320 1.44 1.47 1.50 1.53

325 1.43 1.46 1.49 1.52

330 1.42 1.45 1.48 1.51

335 1.41 1.44 1.47 1.50

340 1.41 1.43 1.46 1.49

345 1.40 1.42 1.45 1.48

350 1.39 1.42 1.44 1.47

355 1.38 1.41 1.43 1.46

360 1.37 1.40 1.42 1.45

365 1.36 1.39 1.42 1.44

370 1.36 1.38 1.41 1.43

375 1.35 1.37 1.40 1.42

Delta H = K factor * Delta P 

# M29

M29-South - U Common Runs 1-3.xls K-Fs R2 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M29

Unit 1 and 2

Normal

Run No: Run 3

Date: 4/27/2010

METER BOX ID: 90594 Orifice Delta H@: 1.842 Y FACTOR: 1.005

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.13 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.842 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 28.88 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 28.73 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 55 65 75 85

270 1.53 1.56 1.59 1.61

275 1.52 1.54 1.57 1.60

280 1.51 1.53 1.56 1.59

285 1.50 1.52 1.55 1.58

290 1.49 1.51 1.54 1.57

295 1.48 1.50 1.53 1.56

300 1.47 1.49 1.52 1.55

305 1.46 1.48 1.51 1.54

310 1.45 1.47 1.50 1.53

315 1.44 1.47 1.49 1.52

320 1.43 1.46 1.48 1.51

325 1.42 1.45 1.47 1.50

330 1.41 1.44 1.46 1.49

335 1.40 1.43 1.46 1.48

340 1.39 1.42 1.45 1.47

345 1.38 1.41 1.44 1.46

350 1.38 1.40 1.43 1.46

355 1.37 1.39 1.42 1.45

360 1.36 1.38 1.41 1.44

365 1.35 1.38 1.40 1.43

370 1.34 1.37 1.39 1.42

375 1.33 1.36 1.39 1.41

380 1.33 1.35 1.38 1.40

385 1.32 1.34 1.37 1.40

390 1.31 1.34 1.36 1.39

395 1.30 1.33 1.35 1.38

Delta H = K factor * Delta P 

# M29

M29-South - U Common Runs 1-3.xls K-Fs R3 

# TRC Environmental Corporation

# NOZZLE SELECTION CALCULATIONS 

# M29

Unit 1 and 2

Normal

CHECK ALL INPUTS

Hand Input or Check Links

Input By:

Run 1 Run 2 Run 3

Date: 4/26/2010 4/27/2010 4/27/2010

Bar. Pressure, Pbar, in. Hg 29.07 29.13 29.13

Stack Temp.(F), ts (from prev. run) 125.0 189.5 187.3

Stack Temp. (R), Ts 585 650 647

Meter Temp. (F), tm 70.0 74.4 90.0

Meter Temp. (R), Tm 530 534 550

Pitot Number 0.0 0.0 0.0

Pitot Coefficient, cp 0.84 0.84 0.84

delta P avg. (from prev. run), dP, in. H2O 

# 0.94 2.20 1.95

O2 avg. (from prev. run), % 5.50 6.55 6.07

CO2 avg. (from prev. run), % 12.00 12.68 13.10

Static Pressure (from prev. run), in. H2O 

# -0.40 -0.85 -0.91

Ps, in. Hg 29.041 29.068 29.063

Mwd, lb/lb mole, dry 30.14 30.29 30.34

% Moisture (from prev. run) 13.0 13.7 13.4

MD 0.870 0.863 0.866

Mws, lb/lb mole, wet 28.562 28.608 28.683

delta H, (for sampling rate), in. H2O 1.731 1.731 1.731

delta H@, in. H2O 1.731 1.842 1.842

Qm, dscfm 0.750 0.727 0.727

Desired Nozzle , inches 0.223 0.182 0.185



# For Standard Test: dH = dH@, and therefore, Qm will be 0.75 dscfm.

For Different Sampling Rate: Input selected dH to yield desired sampling rate.

Desired Nozzle:

SQRT(SQRT((Ts*Mws)/(Ps*dP))*(0.0357*Qm*Pbar)/(Tm*cp*MD)) M29

M29-South - U Common Runs 1-3.xlsNozzles 

# TRC Environmental Corporation

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: 00-Jan-00

LOCATION: Southampton PROJECT NO.: 170096-0030

UNIT: Unit 1 and 2 PERSONNEL: TRC

CONDITION: Normal



# Data Input Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.



# M29

Parameter SYMBOL UNITS DATA Data

Test Number Prelim. Run 1 Run 2 Run 3

Test Date 1/0/1900 4/26/2010 4/27/2010 4/27/2010

Start Time 12:00 09:00 14:45

Stop Time 16:07 13:05 19:05 3-RUN AVG.

Stack Diameter ds inches 96.00 96.00 96.00

Nozzle Diameter dn inches 0.218 0.218 0.218

Barometric Pressure Pbar in. Hg 29.07 29.13 29.13 29.11

Stack Static Pressure Pg in. H2O -0.85 -0.91 -0.91 -0.89

Pitot Coefficient cp none 0.84 0.84 0.84 0.84

Meter Calibration Factor Y none 0.9873 0.9873 0.9873

DH@ none 1.7310 1.7310 1.7310

Stack Gas Oxygen Content O2 % 6.545 6.067 5.995 6.202

Stack Gas Carbon Dioxide Content CO2 % 12.683 13.101 13.178 12.987

Net Moisture Gain (Impingers w/SiGel) Ww grams 781.3 726.3 755.0 754.2

Average Stack Temperature ts deg F 189.5 187.3 186.2 187.7

Average Meter Temperature tm deg F 93.1 84.5 81.3 86.3

Avg Delta H dH in. H2O 3.41 3.03 3.11 3.18

Average Square Root Delta H ASR dH in. H2O 1.840 1.739 1.761 1.780

Avg Velocity Head dP in. H2O 2.20 1.95 2.00 2.05

Average Square Root Delta P ASR dP in H2O 1.478 1.395 1.412 1.428

Gas Sample Volume Vm cu. ft. 251.444 235.301 237.436 241.394

Total Sampling Time min minutes 240 240 240

M29-South - U Common Runs 1-3.xls/Data 6/18/2010 8:40 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 26-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit 1 and 2

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 1 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 48

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

1 0 533.188 1.7 1.304 2.6 1.612 183 81 80

5 1.8 1.342 2.8 1.673 185 84 80

2 1 0 2.0 1.414 3.1 1.761 186 89 82

15 1.9 1.378 2.9 1.703 186 89 81

3 2 0 2.1 1.449 3.3 1.817 187 90 81

25 2.1 1.449 3.3 1.817 187 93 82

4 3 0 2.4 1.549 3.7 1.924 187 96 83

35 2.2 1.483 3.4 1.844 187 98 84

5 4 0 2.5 1.581 3.9 1.975 187 99 85

45 2.5 1.581 3.9 1.975 188 100 86

6 5 0 2.8 1.673 4.3 2.074 190 98 85

55 2.8 1.673 4.3 2.074 192 98 85

7 6 0 2.1 1.449 3.3 1.817 192 98 85

65 2.9 1.703 4.5 2.121 191 102 86

8 7 0 2.7 1.643 4.2 2.049 190 101 86

75 2.9 1.703 4.5 2.121 190 103 87

9 8 0 2.5 1.581 3.9 1.975 189 105 88

85 2.5 1.581 3.9 1.975 189 106 89

10 90 2.4 1.549 3.7 1.924 189 105 90

95 2.5 1.581 3.9 1.975 189 106 90

11 100 2.3 1.517 3.6 1.897 188 107 90

105 2.3 1.517 3.6 1.897 188 105 90

12 110 2.0 1.414 3.1 1.761 189 105 90

115 2.0 1.414 3.1 1.761 188 104 90

13 120 662.251 1.5 1.225 2.3 1.517 186 90 87

125 662.464 1.5 1.225 2.3 1.517 187 92 86

14 130 1.9 1.378 2.9 1.703 186 95 84

135 1.7 1.304 2.6 1.612 187 99 84

15 140 2.0 1.414 3.1 1.761 185 101 85 DIFF

PRESS. 

# M29 

# Field Data Run Sheets

M29-South - U Common Runs 1-3.xls/Run 1 6/18/2010 8:40 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 26-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit 1 and 2

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 1 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 48

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET DIFF

PRESS. 

# M29 

# Field Data Run Sheets

145 2.0 1.414 3.1 1.761 187 103 86

16 150 2.2 1.483 3.4 1.844 187 103 87

155 2.2 1.483 3.4 1.844 188 105 87

17 160 2.3 1.517 3.6 1.897 189 102 87

165 2.2 1.483 3.4 1.844 190 104 89

18 170 2.2 1.483 3.4 1.844 190 105 89

175 2.3 1.517 3.6 1.897 190 105 89

19 180 2.4 1.549 3.7 1.924 191 104 89

185 2.3 1.517 3.6 1.897 192 103 89

20 190 2.4 1.549 3.7 1.924 192 104 89

195 2.5 1.581 3.9 1.975 194 101 88

21 200 2.3 1.517 3.6 1.897 194 104 89

205 2.4 1.549 3.7 1.924 195 104 89

22 210 2.3 1.517 3.6 1.897 195 101 88

215 2.3 1.517 3.6 1.897 196 102 88

23 220 1.7 1.304 2.6 1.612 197 96 86

225 1.7 1.304 2.6 1.612 195 101 86

24 230 1.7 1.304 2.6 1.612 194 99 86

235 1.6 1.265 2.5 1.581 193 101 86

Stop 240 784.845

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

240.0 251.444 2.20 1.478 3.41 1.840 189.5 93.1

Impinger Gain

impinger 1: 948.5 623.5 325.0 O2: 6.545 Start Time: 12:00

impinger 2: 967.5 735.5 232.0 CO2: 12.683 Stop Time: 16:07

impinger 3: 865.5 707.5 158.0

impinger 4: 651.0 641.2 9.8 Static Pressure (Port A): -0.85

Si gel 996.0 939.5 56.5 Static Pressure (Port B): -0.85

Static Pressure (Avg.): -0.85

781.3



# M29-South - U Common Runs 1-3.xls/Run 1 6/18/2010 8:40 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 27-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit 1 and 2

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 2 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 48

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

1 0 785.759 1.4 1.183 2.2 1.483 188 69 68

5 1.4 1.183 2.2 1.483 189 71 68

2 1 0 1.6 1.265 2.5 1.581 188 74 68

15 1.6 1.265 2.5 1.581 191 78 69

3 2 0 1.7 1.304 2.6 1.612 191 81 70

25 1.8 1.342 2.8 1.673 192 84 71

4 3 0 1.9 1.378 2.9 1.703 191 86 72

35 1.8 1.342 2.8 1.673 192 87 74

5 4 0 1.9 1.378 2.9 1.703 191 88 74

45 2.0 1.414 3.1 1.761 191 89 74

6 5 0 2.1 1.449 3.3 1.817 193 90 75

55 2.0 1.414 3.1 1.761 193 92 75

7 6 0 2.1 1.449 3.3 1.817 193 92 76

65 2.1 1.449 3.3 1.817 194 93 77

8 7 0 2.1 1.449 3.3 1.817 194 95 78

75 2.0 1.414 3.1 1.761 194 94 78

9 8 0 2.0 1.414 3.1 1.761 192 93 78

85 2.1 1.449 3.3 1.817 189 95 79

10 90 2.1 1.449 3.3 1.817 187 95 79

95 2.0 1.414 3.1 1.761 187 96 80

11 100 2.0 1.414 3.1 1.761 186 97 81

105 2.0 1.414 3.1 1.761 185 97 81

12 110 1.9 1.378 2.9 1.703 185 96 81

115 1.9 1.378 2.9 1.703 184 97 81

13 120 901.504 1.7 1.304 2.6 1.612 181 83 80

125 901.603 1.8 1.342 2.8 1.670 183 93 81

14 130 1.8 1.342 2.8 1.670 182 95 81

135 1.8 1.342 2.8 1.670 182 96 80

15 140 2.0 1.414 3.1 1.761 181 95 80 DIFF

PRESS. 

# M29 

# Field Data Run Sheets

M29-South - U Common Runs 1-3.xls/Run 2 6/18/2010 8:40 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 27-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit 1 and 2

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 2 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 48

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET DIFF

PRESS. 

# M29 

# Field Data Run Sheets

145 1.9 1.378 2.9 1.703 181 96 81

16 150 1.9 1.378 2.9 1.703 181 95 80

155 2.0 1.414 3.1 1.761 180 95 80

17 160 2.0 1.414 3.1 1.761 180 96 80

165 2.0 1.414 3.1 1.761 180 96 80

18 170 2.1 1.449 3.3 1.817 180 95 80

175 2.1 1.449 3.3 1.817 185 96 80

19 180 2.2 1.483 3.4 1.844 187 96 80

185 2.1 1.449 3.3 1.817 187 96 81

20 190 2.1 1.449 3.3 1.817 188 96 80

195 2.2 1.483 3.4 1.844 188 94 80

21 200 2.1 1.449 3.3 1.817 188 95 80

205 2.1 1.449 3.3 1.817 188 95 80

22 210 2.1 1.449 3.3 1.817 188 93 80

215 2.1 1.449 3.3 1.817 188 93 78

23 220 2.0 1.414 3.1 1.761 188 95 78

225 2.1 1.449 3.3 1.817 188 94 78

24 230 2.0 1.414 3.1 1.761 187 94 78

235 1.9 1.378 2.9 1.703 187 93 78

Stop 240 1021.159

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

240.0 235.301 1.950 1.395 3.03 1.739 187.3 84.5

Impinger Gain

impinger 1: 922.5 624.0 298.5 O2: 6.067 Start Time: 09:00

impinger 2: 943.5 708.0 235.5 CO2: 13.101 Stop Time: 13:05

impinger 3: 836.0 701.0 135.0

impinger 4: 631.0 623.2 7.8 Static Pressure (Port A): -0.91

si gel 1031.0 981.5 49.5 Static Pressure (Port B): -0.91

0.0 Static Pressure (Avg.): -0.91

726.3



# M29-South - U Common Runs 1-3.xls/Run 2 6/18/2010 8:40 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 27-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit 1 and 2

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 3 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 48

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

1 0 21.478 1.4 1.183 2.2 1.483 183 64 62

5 1.5 1.225 2.3 1.517 183 69 62

2 1 0 1.8 1.342 2.9 1.703 188 71 62

15 1.8 1.342 2.8 1.673 186 78 62

3 2 0 1.9 1.378 2.9 1.703 186 81 68

25 1.9 1.378 2.9 1.703 185 83 67

4 3 0 2.0 1.414 3.1 1.761 184 84 67

35 2.0 1.414 3.1 1.761 185 86 68

5 4 0 2.1 1.449 3.3 1.817 186 86 69

45 2.1 1.449 3.3 1.817 186 86 69

6 5 0 2.1 1.449 3.3 1.817 186 84 69

55 2.0 1.414 3.1 1.761 186 88 70

7 6 0 2.2 1.483 3.4 1.844 186 86 70

65 2.2 1.483 3.4 1.844 186 86 70

8 7 0 2.2 1.483 3.4 1.844 187 83 69

75 2.2 1.483 3.4 1.844 187 86 70

9 8 0 2.1 1.449 3.3 1.817 187 89 71

85 2.1 1.449 3.3 1.817 187 88 71

10 90 2.1 1.449 3.3 1.817 187 91 72

95 2.1 1.449 3.3 1.817 186 92 73

11 100 2.1 1.449 3.3 1.817 186 93 74

105 2.0 1.414 3.1 1.761 186 95 75

12 110 1.9 1.378 2.9 1.703 186 95 76

115 1.9 1.378 2.9 1.703 186 95 77

13 120 139.363 1.6 1.265 2.5 1.581 186 76 77

125 139.468 1.6 1.265 2.5 1.581 186 86 75

14 130 1.7 1.304 2.6 1.612 186 90 75

135 1.7 1.304 2.6 1.612 186 91 75

15 140 1.9 1.378 2.9 1.703 186 92 76 DIFF

PRESS. 

# M29 

# Field Data Run Sheets

M29-South - U Common Runs 1-3.xls/Run 3 6/18/2010 8:40 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 27-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Unit 1 and 2

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 3 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 48

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET DIFF

PRESS. 

# M29 

# Field Data Run Sheets

145 1.8 1.342 2.8 1.673 186 94 77

16 150 2.0 1.414 3.1 1.761 186 95 77

155 2.0 1.414 3.1 1.761 187 95 78

17 160 2.0 1.414 3.1 1.761 186 96 78

165 2.1 1.449 3.3 1.817 186 95 78

18 170 2.1 1.449 3.3 1.817 186 96 79

175 2.1 1.449 3.3 1.817 186 97 80

19 180 2.2 1.483 3.4 1.844 187 98 80

185 2.2 1.483 3.4 1.844 186 97 80

20 190 2.2 1.483 3.4 1.844 187 95 80

195 2.3 1.517 3.6 1.897 188 95 79

21 200 2.1 1.449 3.3 1.817 187 96 78

205 2.1 1.449 3.3 1.817 187 95 79

22 210 2.3 1.517 3.6 1.897 187 95 79

215 2.1 1.449 3.3 1.817 187 95 79

23 220 2.1 1.449 3.3 1.817 187 92 78

225 2.0 1.414 3.1 1.761 187 93 77

24 230 2.0 1.414 3.1 1.761 187 91 77

235 2.0 1.414 3.1 1.761 187 92 76

Stop 240 259.019

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

240.0 237.436 1.998 1.412 3.11 1.761 186.2 81.3

Impinger Gain

impinger 1: 945.5 626.0 319.5 O2: 5.995 Start Time: 14:45

impinger 2: 978.0 735.0 243.0 CO2: 13.178 Stop Time: 19:05

impinger 3: 843.0 707.0 136.0

impinger 4: 649.5 642.0 7.5 Static Pressure (Port A): -0.91

si gel 973.5 924.5 49.0 Static Pressure (Port B): -0.91

Static Pressure (Avg.): -0.91

755.0



# M29-South - U Common Runs 1-3.xls/Run 3 6/18/2010 8:40 PM

# L2010-275 

# APPENDIX A.5

MERCURY FIELD SAMPLING DATAHg TESTPARAMETERS 4/26/2010 12:00 PMXducerPitotBarom Flow 1Vac 1 Flow 2 Vac 2 aux LoadGain1.12 3.410.17 1100 0.189 1100 10Offset0.001 17.40.004 0.5 0.004 0.5 00TstdPstdGam 1 Gam 2CPL 2 CPL 16829.92 1.00130.9812 526.106 526.211Prop timeProbe min Filter min Stack min Test time0.5225 250150 240LpmMotor V Log Time File Suffix Load Proportion0.82.6 60 South 4-26-10 r1 Pitot ManualTime:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/26/2010,12:00:320 28.4170.813 3.346 0.859 3.233 00 185.51504/26/2010,12:01:320 28.4150.888 2.952 0.987 2.855 00 185.39104/26/2010,12:02:330 28.4130.888 2.845 0.987 2.85 00 185.37804/26/2010,12:03:330 28.4120.888 2.823 0.986 2.847 00 185.42904/26/2010,12:04:330 28.410.888 2.773 0.985 2.858 00 185.32404/26/2010,12:05:330 28.4110.888 2.85 0.985 2.848 00 185.40304/26/2010,12:06:330 28.410.888 2.781 0.984 2.846 00 185.71704/26/2010,12:07:330 28.4080.887 2.817 0.984 2.839 00 185.78204/26/2010,12:08:330 28.4080.887 2.753 0.984 2.839 00 185.75304/26/2010,12:09:330 28.4040.887 2.729 0.983 2.837 00 185.75904/26/2010,12:10:330 28.4020.887 2.818 0.983 2.842 00 185.70104/26/2010,12:11:330 28.40.887 2.776 0.983 2.838 00 185.59504/26/2010,12:12:330 28.40.887 2.828 0.983 2.843 00 185.55404/26/2010,12:13:330 28.3990.886 2.809 0.983 2.839 00 185.6104/26/2010,12:14:330 28.4010.886 2.783 0.982 2.842 00 185.72504/26/2010,12:15:330 28.4040.886 2.786 0.982 2.846 00 185.56504/26/2010,12:16:330 28.3960.886 2.813 0.982 2.836 00 185.86604/26/2010,12:17:330 28.3930.886 2.772 0.982 2.837 00 186.05604/26/2010,12:18:330 28.3990.886 2.854 0.982 2.839 00 186.06204/26/2010,12:19:330 28.4010.886 2.834 0.982 2.835 00 185.93804/26/2010,12:20:330 28.3950.886 2.758 0.982 2.835 00 185.9604/26/2010,12:21:330 28.3950.886 2.756 0.982 2.832 00 186.02204/26/2010,12:22:330 28.3950.886 2.724 0.982 2.83 00 18604/26/2010,12:23:330 28.3950.886 2.709 0.982 2.832 00 186.07104/26/2010,12:24:330 28.3910.886 2.728 0.982 2.83 00 186.27404/26/2010,12:25:330 28.3910.886 2.803 0.982 2.831 00 186.08504/26/2010,12:26:330 28.3970.886 2.834 0.982 2.83 00 186.09804/26/2010,12:27:340 28.3930.886 2.788 0.982 2.825 00 186.35404/26/2010,12:28:340 28.3920.886 2.861 0.982 2.829 00 186.31604/26/2010,12:29:340 28.3930.886 2.709 0.982 2.827 00 186.15204/26/2010,12:30:340 28.3940.886 2.824 0.981 2.827 00 186.18804/26/2010,12:31:340 28.3880.886 2.79 0.981 2.822 00 186.21104/26/2010,12:32:340 28.3850.886 2.729 0.981 2.823 00 186.34804/26/2010,12:33:340 28.3750.886 2.822 0.981 2.827 00 186.60204/26/2010,12:34:340 28.3820.886 2.753 0.981 2.823 00 186.8704/26/2010,12:35:340 28.3840.885 2.803 0.981 2.826 00 187.19704/26/2010,12:36:340 28.3840.885 2.834 0.981 2.824 00 186.88704/26/2010,12:37:340 28.3830.885 2.794 0.981 2.827 00 187.084Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/26/2010,12:00:3204/26/2010,12:01:3204/26/2010,12:02:3304/26/2010,12:03:3304/26/2010,12:04:3304/26/2010,12:05:3304/26/2010,12:06:3304/26/2010,12:07:3304/26/2010,12:08:3304/26/2010,12:09:3304/26/2010,12:10:3304/26/2010,12:11:3304/26/2010,12:12:3304/26/2010,12:13:3304/26/2010,12:14:3304/26/2010,12:15:3304/26/2010,12:16:3304/26/2010,12:17:3304/26/2010,12:18:3304/26/2010,12:19:3304/26/2010,12:20:3304/26/2010,12:21:3304/26/2010,12:22:3304/26/2010,12:23:3304/26/2010,12:24:3304/26/2010,12:25:3304/26/2010,12:26:3304/26/2010,12:27:3404/26/2010,12:28:3404/26/2010,12:29:3404/26/2010,12:30:3404/26/2010,12:31:3404/26/2010,12:32:3404/26/2010,12:33:3404/26/2010,12:34:3404/26/2010,12:35:3404/26/2010,12:36:3404/26/2010,12:37:34Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFdegF degFdegF degFdegF degF degFliters STP liters STP liters nominal liters nominal77.809 250.64180.784 80.073500 81.37 83.49381.852 2.657 2.712 2.858 2.98478.375 252.51880.771 79.991500 81.401 83.70281.966 5.574 5.699 5.996 6.27178.846 249.42680.882 80.097500 81.46 83.91682.084 8.616 8.68 9.268 9.55179.518 252.79480.974 80.064500 81.495 84.17982.196 11.694 11.617 12.579 12.78479.35 250.78381.154 80.113500 81.618 84.27482.312 14.799 14.576 15.919 16.04278.391 250.55381.379 80.205500 81.683 84.27782.427 17.847 17.542 19.2 19.30877.639 251.76181.523 80.293500 81.76 84.21182.543 20.918 20.517 22.504 22.58577.667 248.69581.595 80.349500 81.866 84.28882.657 23.993 23.516 25.815 25.88878.384 251.84581.618 80.417500 81.946 84.49582.772 27.041 26.478 29.097 29.15278.887 250.62481.68 80.481500 81.993 84.60682.886 30.128 29.43 32.42 32.40479.568 249.5381.751 80.599500 82.065 84.79683.001 33.242 32.389 35.775 35.66680.396 252.82481.918 80.667500 82.15 84.92683.112 36.281 35.389 39.049 38.97380.726 249.60782.02 80.739500 82.263 84.98883.225 39.335 38.326 42.34 42.21281.062 251.8982.16380.8500 82.331 85.09783.342 42.4 41.29 45.643 45.48180.987 251.75582.316 80.942500 82.411 85.22383.457 45.436 44.246 48.916 48.74180.044 249.43982.412 81.03500 82.544 85.26683.572 48.526 47.209 52.247 52.0179.705 252.58982.458 81.086500 82.645 85.34883.686 51.621 50.199 55.584 55.3180.557 249.98982.584 81.194500 82.738 85.45683.798 54.648 53.155 58.849 58.57480.536 251.00982.529 81.303500 82.808 85.50383.911 57.695 56.091 62.137 61.81580.097 252.32582.422 81.361500 82.929 85.45284.024 60.769 59.056 65.453 65.08879.851 249.44682.374 81.446500 83.004 85.40284.138 63.814 62.052 68.739 68.39779.939 252.54682.421 81.529500 83.073 85.46284.252 66.908 64.993 72.078 71.64580.16 250.94882.517 81.616500 83.125 85.59384.362 69.994 67.965 75.409 74.92879.162 250.04282.707 81.685500 83.251 85.63484.473 73.023 70.917 78.679 78.1978.991 252.36282.829 81.738500 83.302 85.75984.585 76.068 73.878 81.967 81.46379.239 249.10882.904 81.845500 83.357 85.85584.696 79.143 76.89 85.289 84.79178.304 251.09883.1 81.912500 83.414 85.66384.806 82.196 79.819 88.586 88.02877.683 250.683.089 81.989500 83.455 85.6684.914 85.289 82.773 91.927 91.29377.762 248.9482.966 82.026500 83.511 85.76185.016 88.388 85.747 95.275 94.58277.717 251.72882.929 82.067500 83.552 85.79685.117 91.42 88.718 98.552 97.86677.36 248.52282.902 82.115500 83.583 85.88885.218 94.486 91.713 101.864 101.17777.319 250.61582.731 82.142500 83.597 85.95185.316 97.563 94.653 105.19 104.4377.475 251.74782.625 82.228500 83.618 86.0385.413 100.611 97.611 108.485 107.70177.753 248.85682.476 82.245500 83.626 86.17185.507 103.676 100.581 111.799 110.98777.985 252.08382.417 82.273500 83.66 86.20185.601 106.788 103.559 115.165 114.28177.778 250.25982.511 82.305500 83.687 86.15485.694 109.852 106.557 118.477 117.59877.568 249.97182.606 82.322500 83.703 86.07485.789 112.906 109.495 121.78 120.84877.474 252.27182.9 82.348500 83.717 85.8985.879 115.973 112.44 125.096 124.106Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/26/2010,12:38:340 28.3820.885 2.918 0.981 2.826 00 187.34404/26/2010,12:39:340 28.380.885 2.864 0.981 2.828 00 187.54304/26/2010,12:40:340 28.3820.885 2.83 0.981 2.829 00 187.65504/26/2010,12:41:340 28.3830.885 2.83 0.981 2.849 00 188.05104/26/2010,12:42:340 28.3780.885 2.762 0.981 2.828 00 188.39804/26/2010,12:43:340 28.3780.885 2.66 0.981 2.825 00 188.81204/26/2010,12:44:340 28.3790.885 2.735 0.981 2.826 00 189.2204/26/2010,12:45:340 28.3770.885 2.832 0.981 2.824 00 189.61404/26/2010,12:46:340 28.3760.885 2.8 0.981 2.844 00 189.83504/26/2010,12:47:340 28.3820.885 2.82 0.981 2.884 00 189.9504/26/2010,12:48:340 28.390.885 2.987 0.981 2.918 00 190.84504/26/2010,12:49:340 28.3770.885 2.804 0.981 2.882 00 190.59404/26/2010,12:50:340 28.3810.885 2.853 0.981 2.875 00 190.86604/26/2010,12:51:350 28.3750.885 2.799 0.981 2.868 00 190.80704/26/2010,12:52:350 28.3780.885 2.713 0.981 2.865 00 191.00804/26/2010,12:53:350 28.3780.885 2.828 0.981 2.859 00 191.27304/26/2010,12:54:350 28.3810.885 2.752 0.981 2.859 00 191.51104/26/2010,12:55:350 28.3760.885 2.79 0.981 2.861 00 191.63904/26/2010,12:56:350 28.3720.885 2.971 0.981 2.859 00 191.68404/26/2010,12:57:350 28.3740.885 2.855 0.981 2.857 00 191.53604/26/2010,12:58:350 28.3710.885 2.644 0.981 2.856 00 190.78604/26/2010,12:59:350 28.3710.885 2.793 0.981 2.86 00 190.4304/26/2010,13:00:350 28.3720.885 2.701 0.981 2.854 00 190.50104/26/2010,13:01:350 28.370.885 2.824 0.981 2.858 00 190.45804/26/2010,13:02:350 28.3680.885 2.817 0.981 2.855 00 190.37904/26/2010,13:03:350 28.3690.885 2.747 0.981 2.858 00 190.29904/26/2010,13:04:350 28.3690.885 2.819 0.981 2.859 00 190.22704/26/2010,13:05:350 28.3680.885 2.777 0.981 2.857 00 190.09404/26/2010,13:06:350 28.3690.885 2.804 0.981 2.86 00 189.93304/26/2010,13:07:350 28.3680.885 2.754 0.981 2.86 00 189.78304/26/2010,13:08:350 28.3690.885 2.758 0.981 2.859 00 189.62104/26/2010,13:09:350 28.3670.885 2.776 0.981 2.856 00 189.72104/26/2010,13:10:350 28.3680.885 2.766 0.981 2.863 00 189.8104/26/2010,13:11:350 28.3680.885 2.742 0.981 2.864 00 189.80404/26/2010,13:12:350 28.3680.885 2.899 0.981 2.862 00 189.60504/26/2010,13:13:350 28.370.885 2.767 0.981 2.865 00 189.48404/26/2010,13:14:350 28.3710.885 2.889 0.981 2.866 00 189.3804/26/2010,13:15:360 28.3740.885 2.73 0.981 2.863 00 189.2304/26/2010,13:16:360 28.3740.885 2.768 0.981 2.863 00 189.10604/26/2010,13:17:360 28.3750.885 2.81 0.981 2.868 00 189.09104/26/2010,13:18:360 28.3760.885 2.756 0.981 2.864 00 188.87504/26/2010,13:19:360 28.3750.885 2.837 0.981 2.862 00 188.97304/26/2010,13:20:360 28.3770.885 2.979 0.981 2.861 00 189.12804/26/2010,13:21:360 28.3780.885 2.798 0.981 2.861 00 189.16204/26/2010,13:22:360 28.3770.885 2.899 0.981 2.86 00 189.20104/26/2010,13:23:360 28.3760.885 2.766 0.981 2.86 00 189.07704/26/2010,13:24:360 28.3760.885 2.705 0.981 2.861 00 189.0104/26/2010,13:25:360 28.3750.885 2.808 0.981 2.856 00 188.93304/26/2010,13:26:360 28.3760.885 2.838 0.981 2.86 00 188.86704/26/2010,13:27:360 28.3750.885 2.771 0.981 2.862 00 188.9504/26/2010,13:28:360 28.3770.885 2.8 0.981 2.859 00 188.89Time:date,hh:mm:ss04/26/2010,12:38:3404/26/2010,12:39:3404/26/2010,12:40:3404/26/2010,12:41:3404/26/2010,12:42:3404/26/2010,12:43:3404/26/2010,12:44:3404/26/2010,12:45:3404/26/2010,12:46:3404/26/2010,12:47:3404/26/2010,12:48:3404/26/2010,12:49:3404/26/2010,12:50:3404/26/2010,12:51:3504/26/2010,12:52:3504/26/2010,12:53:3504/26/2010,12:54:3504/26/2010,12:55:3504/26/2010,12:56:3504/26/2010,12:57:3504/26/2010,12:58:3504/26/2010,12:59:3504/26/2010,13:00:3504/26/2010,13:01:3504/26/2010,13:02:3504/26/2010,13:03:3504/26/2010,13:04:3504/26/2010,13:05:3504/26/2010,13:06:3504/26/2010,13:07:3504/26/2010,13:08:3504/26/2010,13:09:3504/26/2010,13:10:3504/26/2010,13:11:3504/26/2010,13:12:3504/26/2010,13:13:3504/26/2010,13:14:3504/26/2010,13:15:3604/26/2010,13:16:3604/26/2010,13:17:3604/26/2010,13:18:3604/26/2010,13:19:3604/26/2010,13:20:3604/26/2010,13:21:3604/26/2010,13:22:3604/26/2010,13:23:3604/26/2010,13:24:3604/26/2010,13:25:3604/26/2010,13:26:3604/26/2010,13:27:3604/26/2010,13:28:36Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFdegF degFdegF degFdegF degF degFliters STP liters STP liters nominal liters nominal77.63 249.27482.736 82.362500 83.718 85.92585.969 119.041 115.426 128.414 127.4178.209 251.68682.667 82.38500 83.731 86.10586.056 122.091 118.398 131.713 130.69878.567 251.73882.748 82.405500 83.755 86.20386.142 125.173 121.385 135.047 134.00378.218 249.46982.955 82.458500 83.805 86.06686.228 128.272 124.338 138.399 137.27196.702 252.50582.934 82.494500 83.82 85.91186.31 131.331 127.275 141.707 140.52181.683 249.03982.712 82.527500 83.834 86.01386.388 134.404 130.256 145.033 143.82197.844 251.39682.607 82.57500 83.883 86.20586.468 137.424 133.236 148.3 147.11982.054 251.63282.608 82.581500 83.907 86.21486.547 140.5 136.215 151.629 150.416167.594 249.48282.541 82.595500 83.922 86.19586.624 143.561 139.175 154.942 153.693309.297 253.18982.586 82.691500 83.964 86.28986.706 146.647 142.117 158.281 156.949302.231 249.1884.096 84.321500 84.799 86.0386.805 149.736 145.066 161.633 160.219290.217 251.90382.463 82.628500 83.961 86.37386.852 152.804 148.033 164.953 163.503278.847 251.86682.309 82.639500 83.975 86.34386.929 155.879 150.951 168.28 166.733270.768 249.80382.177 82.643500 83.975 86.47887.001 158.949 153.876 171.602 169.971270.375 253.13782.147 82.649500 83.984 86.53387.07 162.064 156.838 174.974 173.25272.979 250.26882.08 82.646500 83.985 86.45887.14 165.148 159.806 178.311 176.537272.031 251.40182.135 82.65450084 86.34187.209 168.237 162.768 181.653 179.815270.476 251.96682.116 82.644500 83.998 86.32887.275 171.343 165.735 185.015 183.1271.286 250.07982.004 82.647500 83.994 86.33687.342 174.461 168.665 188.39 186.345271.574 253.20882.088 82.652500 83.998 86.32887.409 177.588 171.619 191.775 189.616270.961 250.1682.12 82.654500 83.994 86.44987.47 180.698 174.609 195.14 192.927271.118 251.582.114 82.653500 83.982 86.53187.531 183.772 177.548 198.468 196.181271.54 252.55382.217 82.65500 83.976 86.40287.589 186.872 180.507 201.824 199.458271.346 249.41982.183 82.649500 83.963 86.1987.646 189.978 183.449 205.186 202.716271.376 252.68482.189 82.639500 83.943 86.13887.7 193.059 186.414 208.521 205.998271.724 250.53882.095 82.637500 83.923 86.04187.753 196.187 189.414 211.907 209.321271.768 250.80682.056 82.646500 83.924 86.00787.802 199.289 192.334 215.265 212.554271.968 252.95482.023 82.634500 83.904 86.15187.849 202.38 195.283 218.612 215.82272.134 249.76381.959 82.614500 83.891 86.22287.895 205.482 198.248 221.97 219.102272.189 252.82982.023 82.62500 83.898 86.38587.939 208.602 201.212 225.347 222.385272.359 252.06182.024 82.624500 83.896 86.41787.986 211.725 204.191 228.728 225.683272.386 250.8582.016 82.609500 83.888 86.3288.028 214.841 207.152 232.101 228.961272.366 253.8282.141 82.624500 83.912 86.39688.072 217.929 210.087 235.444 232.212272.669 250.41482.252 82.629500 83.922 86.52388.115 221.003 213.033 238.771 235.473272.742 252.56882.269 82.622500 83.931 86.53688.161 224.112 216.021 242.137 238.783272.84 252.72282.363 82.661500 83.955 86.56388.208 227.197 218.957 245.476 242.033272.917 250.13382.496 82.664500 83.982 86.61788.251 230.295 221.911 248.83 245.304272.891 253.39482.575 82.668500 84.001 86.56388.295 233.394 224.853 252.184 248.562273.015 250.1682.699 82.717500 84.029 86.48588.337 236.486 227.809 255.531 251.835273.057 251.782.656 82.715500 84.032 86.51288.379 239.581 230.797 258.881 255.144273.26 251.88582.683 82.729500 84.067 86.48488.424 242.711 233.729 262.269 258.391273.272 249.88282.615 82.761500 84.08 86.53788.459 245.838 236.664 265.654 261.641273.345 252.98582.646 82.769500 84.076 86.49688.499 248.922 239.637 268.993 264.933273.501 249.64682.718 82.82500 84.168 86.46588.535 252.021 242.614 272.347 268.229273.43 251.49882.675 82.809500 84.137 86.31588.574 255.13 245.574 275.713 271.508273.47 251.78582.655 82.872500 84.179 86.32688.609 258.221 248.543 279.059 274.796273.652 249.72482.579 82.846500 84.17 86.37988.647 261.305 251.476 282.398 278.045273.816 252.982.487 82.884500 84.193 86.4888.679 264.436 254.43 285.788 281.316273.791 250.02782.519 82.879500 84.203 86.50288.712 267.522 257.421 289.129 284.629273.789 251.35382.483 82.891500 84.219 86.588.744 270.611 260.362 292.474 287.887273.957 252.23682.417 82.847500 84.185 86.50388.775 273.721 263.323 295.841 291.166Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/26/2010,13:29:360 28.3750.885 2.718 0.981 2.859 00 188.74704/26/2010,13:30:360 28.3760.885 2.71 0.981 2.857 00 189.04504/26/2010,13:31:360 28.3760.885 2.742 0.981 2.853 00 189.11704/26/2010,13:32:360 28.3740.885 2.696 0.981 2.857 00 188.96404/26/2010,13:33:360 28.3740.885 3.034 0.981 2.859 00 188.86604/26/2010,13:34:360 28.3760.885 2.725 0.981 2.856 00 188.64904/26/2010,13:35:360 28.3730.885 2.726 0.981 2.859 00 188.56104/26/2010,13:36:360 28.3720.885 2.656 0.981 2.858 00 188.54504/26/2010,13:37:360 28.3720.885 2.937 0.981 2.859 00 188.59204/26/2010,13:38:360 28.3730.885 2.862 0.981 2.855 00 188.90904/26/2010,13:39:370 28.3680.885 2.848 0.981 2.855 00 188.53804/26/2010,13:40:370 28.3680.885 2.665 0.981 2.854 00 188.30604/26/2010,13:41:370 28.3660.885 2.697 0.981 2.854 00 188.53804/26/2010,13:42:370 28.3640.885 2.643 0.981 2.853 00 188.55304/26/2010,13:43:370 28.3640.885 2.674 0.981 2.857 00 188.59104/26/2010,13:44:370 28.3620.885 2.802 0.981 2.857 00 188.64304/26/2010,13:45:370 28.3610.885 2.674 0.981 2.853 00 188.78804/26/2010,13:46:370 28.3590.885 2.593 0.981 2.85 00 188.83304/26/2010,13:47:370 28.360.885 2.822 0.981 2.86 00 188.93104/26/2010,13:51:150 28.3660.885 2.821 0.981 2.88 00 188.72404/26/2010,13:52:150 28.3660.885 2.821 0.981 2.882 00 188.64804/26/2010,13:53:150 28.3660.885 2.77 0.981 2.879 00 188.65604/26/2010,13:54:160 28.3650.885 2.886 0.981 2.881 00 188.79504/26/2010,13:55:160 28.3640.885 2.775 0.981 2.885 00 188.76504/26/2010,13:56:160 28.3620.885 2.775 0.981 2.885 00 188.84104/26/2010,13:57:160 28.360.885 2.716 0.981 2.885 00 188.67604/26/2010,13:58:160 28.3580.885 2.665 0.981 2.887 00 188.62604/26/2010,13:59:160 28.3560.885 2.699 0.981 2.886 00 188.50404/26/2010,14:00:160 28.3570.885 2.757 0.981 2.885 00 188.49604/26/2010,14:01:160 28.3580.885 2.885 0.981 2.885 00 188.39204/26/2010,14:02:160 28.3610.885 2.763 0.981 2.887 00 188.30204/26/2010,14:03:160 28.3620.885 2.786 0.981 2.889 00 188.25704/26/2010,14:04:160 28.3640.885 2.883 0.981 2.887 00 188.32304/26/2010,14:05:160 28.3690.885 2.841 0.981 2.888 00 188.48904/26/2010,14:06:160 28.3720.885 2.738 0.981 2.889 00 188.41404/26/2010,14:07:160 28.3750.885 2.628 0.981 2.889 00 188.41504/26/2010,14:08:160 28.3790.885 2.771 0.981 2.886 00 188.26304/26/2010,14:09:160 28.3760.885 2.795 0.981 2.886 00 188.20604/26/2010,14:10:160 28.3760.885 2.713 0.981 2.887 00 188.24104/26/2010,14:11:160 28.3750.885 2.828 0.981 2.889 00 188.01104/26/2010,14:12:160 28.3740.885 2.791 0.981 2.886 00 187.904/26/2010,14:13:160 28.3670.885 2.751 0.981 2.883 00 187.83104/26/2010,14:14:160 28.3640.885 2.802 0.981 2.89 00 187.82404/26/2010,14:15:160 28.3640.885 2.831 0.981 2.887 00 187.77104/26/2010,14:16:160 28.3650.885 2.948 0.981 2.885 00 187.58604/26/2010,14:17:160 28.3610.885 2.727 0.981 2.888 00 187.56204/26/2010,14:18:170 28.360.885 2.747 0.981 2.896 00 187.58604/26/2010,14:19:170 28.3580.885 2.823 0.981 2.895 00 187.56404/26/2010,14:20:170 28.3570.885 2.914 0.981 2.891 00 187.55304/26/2010,14:21:170 28.3550.885 2.82 0.981 2.903 00 187.59804/26/2010,14:22:170 28.3530.885 2.675 0.981 2.908 00 187.499Time:date,hh:mm:ss04/26/2010,13:29:3604/26/2010,13:30:3604/26/2010,13:31:3604/26/2010,13:32:3604/26/2010,13:33:3604/26/2010,13:34:3604/26/2010,13:35:3604/26/2010,13:36:3604/26/2010,13:37:3604/26/2010,13:38:3604/26/2010,13:39:3704/26/2010,13:40:3704/26/2010,13:41:3704/26/2010,13:42:3704/26/2010,13:43:3704/26/2010,13:44:3704/26/2010,13:45:3704/26/2010,13:46:3704/26/2010,13:47:3704/26/2010,13:51:1504/26/2010,13:52:1504/26/2010,13:53:1504/26/2010,13:54:1604/26/2010,13:55:1604/26/2010,13:56:1604/26/2010,13:57:1604/26/2010,13:58:1604/26/2010,13:59:1604/26/2010,14:00:1604/26/2010,14:01:1604/26/2010,14:02:1604/26/2010,14:03:1604/26/2010,14:04:1604/26/2010,14:05:1604/26/2010,14:06:1604/26/2010,14:07:1604/26/2010,14:08:1604/26/2010,14:09:1604/26/2010,14:10:1604/26/2010,14:11:1604/26/2010,14:12:1604/26/2010,14:13:1604/26/2010,14:14:1604/26/2010,14:15:1604/26/2010,14:16:1604/26/2010,14:17:1604/26/2010,14:18:1704/26/2010,14:19:1704/26/2010,14:20:1704/26/2010,14:21:1704/26/2010,14:22:17Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFdegF degFdegF degFdegF degF degFliters STP liters STP liters nominal liters nominal274.021 249.63782.507 82.89500 84.232 86.4788.808 276.843 266.264 299.222 294.424273.934 252.75682.489 82.856500 84.193 86.28488.84 279.973 269.229 302.611 297.708274.105 250.24382.465 82.891500 84.222 86.27288.871 283.092 272.232 305.988 301.034274.112 250.98782.39 82.85500 84.184 86.29588.903 286.17 275.169 309.321 304.287274.13 252.67782.442 82.876500 84.208 86.36488.931 289.261 278.125 312.667 307.562274.114 249.55382.605 82.884500 84.18 86.24588.958 292.38 281.07 316.044 310.823274.161 252.83282.591 82.858500 84.17 86.24788.987 295.455 284.035 319.374 314.108274.243 250.63682.486 82.889500 84.18 86.2289.011 298.57 287.043 322.747 317.44274.128 250.68782.272 82.845500 84.125 86.28389.034 301.676 289.959 326.111 320.669274.223 252.67682.305 82.858500 84.139 86.27689.061 304.763 292.916 329.453 323.944274.26 249.1982.214 82.86500 84.134 86.28789.085 307.871 295.886 332.819 327.234274.128 252.34682.05 82.781500 84.069 86.28789.106 310.981 298.851 336.186 330.519274.418 251.11482.161 82.812500 84.104 86.33589.127 314.103 301.849 339.567 333.84274.457 250.10181.92 82.777500 84.076 86.16289.146 317.233 304.786 342.957 337.094274.332 252.51281.731 82.734500 84.055 85.95689.168 320.343 307.734 346.325 340.359274.52 249.18281.702 82.727500 84.04 86.08489.189 323.428 310.704 349.666 343.649274.423 252.55781.811 82.72500 84.026 86.2689.21 326.53 313.679 353.026 346.945274.508 250.42781.954 82.679500 84.007 86.52489.23 329.652 316.673 356.406 350.262274.554 251.98682.098 82.672500 83.993 86.77189.269 340.917 327.385 368.603 362.127274.757 249.67782.029 82.634500 83.973 86.9989.343 344.031 330.337 371.974 365.396274.696 252.86881.958 82.606500 83.954 86.98289.37 347.127 333.268 375.327 368.642274.704 250.85782.008 82.594500 83.952 86.97589.397 350.213 336.198 378.667 371.887274.68 250.95981.941 82.593500 83.956 86.95389.423 353.314 339.127 382.024 375.132274.618 252.93581.912 82.571500 83.947 86.90989.45 356.438 342.074 385.406 378.395274.676 249.97981.779 82.584500 83.956 86.96689.477 359.549 344.996 388.774 381.632274.637 252.59181.674 82.554500 83.948 86.97689.504 362.638 347.926 392.118 384.877274.613 251.46281.661 82.544500 83.94 86.95289.529 365.729 350.851 395.465 388.118274.786 250.47681.625 82.553500 83.953 86.94489.553 368.823 353.797 398.815 391.381274.635 253.06381.485 82.474500 83.909 86.99389.581 371.9 356.716 402.147 394.614274.599 249.59881.489 82.531500 83.947 86.99989.604 375.019 359.633 405.524 397.846167.189 252.26981.47 82.457500 83.917 86.87989.626 378.098 362.559 408.857 401.086275.895 250.63981.395 82.429500 83.888 86.74189.648 381.187 365.521 412.2 404.367275.024 250.54581.359 82.443500 83.903 86.65189.671 384.3 368.427 415.569 407.585274.206 252.72881.333 82.41500 83.87 86.6189.694 387.417 371.336 418.942 410.807275.015 249.8281.32 82.394500 83.813 86.60689.716 390.544 374.271 422.325 414.055275.006 252.69681.313 82.414500 83.844 86.57589.739 393.656 377.247 425.692 417.349274.455 250.29981.187 82.373500 83.789 86.37689.758 396.733 380.148 429.02 420.56274.653 251.07380.996 82.325500 83.742 86.15789.777 399.838 383.073 432.378 423.797274.984 252.79280.82 82.309500 83.733 8689.794 402.932 385.996 435.724 427.032274.745 249.88780.72 82.28500 83.715 85.90489.811 406.008 388.963 439.052 430.314274.631 252.8480.527 82.23500 83.666 85.68689.823 409.124 391.895 442.421 433.559274.918 251.4380.432 82.109500 83.609 85.46389.832 412.229 394.804 445.779 436.779274.778 251.1580.286 82.046500 83.551 85.41589.836 415.314 397.729 449.116 440.016274.748 253.68280.193 81.999500 83.46 85.42689.838 418.426 400.7 452.482 443.304253.988 250.25980.125 81.948500 83.423 85.33889.836 421.556 403.631 455.867 446.54778.156 253.38480.093 81.899500 83.393 85.31989.833 424.667 406.527 459.23 449.75277.837 252.34480.105 81.846500 83.35 85.39289.829 427.746 409.46 462.56 452.99680.434 251.12880.23 81.771500 83.337 85.32989.823 430.834 412.399 465.899 456.24885.437 254.09580.299 81.731500 83.318 85.26689.818 433.912 415.319 469.226 459.4898.537 250.59780.389 81.717500 83.289 85.32889.811 437.009 418.227 472.575 462.698112.307 253.57280.467 81.673500 83.282 85.32289.808 440.089 421.169 475.904 465.954Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/26/2010,14:23:170 28.3510.885 2.723 0.981 2.907 00 187.80604/26/2010,14:24:170 28.3520.885 2.855 0.981 2.907 00 187.89704/26/2010,14:25:170 28.3530.885 2.868 0.981 2.91 00 187.82804/26/2010,14:26:170 28.3520.885 2.778 0.981 2.913 00 187.76304/26/2010,14:27:170 28.3530.885 2.809 0.981 2.909 00 187.80704/26/2010,14:28:170 28.3530.885 2.829 0.981 2.917 00 187.85104/26/2010,14:29:170 28.3540.885 2.893 0.981 2.917 00 187.68204/26/2010,14:30:170 28.3540.885 2.797 0.981 2.916 00 187.58704/26/2010,14:31:170 28.3510.885 2.809 0.981 2.919 00 187.64904/26/2010,14:32:170 28.3510.885 2.777 0.981 2.919 00 187.62704/26/2010,14:33:170 28.3490.885 2.9 0.981 2.923 00 187.70304/26/2010,14:34:170 28.3490.885 2.866 0.981 2.921 00 187.99204/26/2010,14:35:170 28.3480.885 2.72 0.981 2.926 00 188.17904/26/2010,14:36:170 28.3470.885 2.751 0.981 2.927 00 188.27204/26/2010,14:37:170 28.3440.885 3.099 0.981 2.924 00 188.29304/26/2010,14:38:170 28.3450.885 2.858 0.981 2.923 00 188.38404/26/2010,14:39:170 28.3450.885 2.713 0.981 2.927 00 188.62504/26/2010,14:40:170 28.340.885 2.898 0.981 2.929 00 188.97704/26/2010,14:41:170 28.3410.885 2.937 0.981 2.931 00 189.21104/26/2010,14:42:170 28.340.885 2.848 0.981 2.93 00 189.53304/26/2010,14:43:180 28.340.885 2.918 0.981 2.931 00 189.1104/26/2010,14:44:180 28.3380.885 2.81 0.981 2.932 00 189.33204/26/2010,14:45:180 28.3350.885 2.847 0.981 2.925 00 189.63504/26/2010,14:46:180 28.3340.885 2.75 0.981 2.925 00 189.52904/26/2010,14:47:180 28.3360.885 2.775 0.981 2.927 00 189.53504/26/2010,14:48:180 28.3390.885 2.756 0.981 2.924 00 189.65204/26/2010,14:49:180 28.3390.885 2.861 0.981 2.919 00 189.73404/26/2010,14:50:180 28.3350.885 2.762 0.981 2.917 00 189.81404/26/2010,14:51:180 28.3350.885 2.713 0.981 2.91 00 189.82104/26/2010,14:52:180 28.3360.885 2.841 0.981 2.907 00 189.95804/26/2010,14:53:180 28.3360.885 2.846 0.981 2.907 00 189.9104/26/2010,14:54:180 28.3350.885 2.761 0.981 2.905 00 189.76904/26/2010,14:55:180 28.3340.885 2.673 0.981 2.904 00 189.85604/26/2010,14:56:180 28.3320.885 2.805 0.981 2.905 00 189.94404/26/2010,14:57:180 28.330.885 2.849 0.981 2.908 00 190.14204/26/2010,14:58:180 28.3280.885 2.68 0.981 2.9 00 190.34604/26/2010,14:59:180 28.3290.885 2.774 0.981 2.901 00 190.52704/26/2010,15:00:180 28.3280.885 2.71 0.981 2.901 00 190.73204/26/2010,15:01:180 28.3240.885 2.871 0.981 2.904 00 190.86204/26/2010,15:02:180 28.3270.885 2.878 0.981 2.903 00 191.15404/26/2010,15:03:180 28.3270.885 2.917 0.981 2.904 00 191.3504/26/2010,15:04:180 28.3230.885 2.745 0.981 2.902 00 191.28304/26/2010,15:05:180 28.3240.885 2.842 0.981 2.902 00 191.28704/26/2010,15:06:180 28.3210.885 2.832 0.981 2.9 00 191.40304/26/2010,15:07:190 28.3210.885 2.772 0.981 2.898 00 191.61604/26/2010,15:08:190 28.3220.885 2.788 0.981 2.903 00 191.85104/26/2010,15:09:190 28.3190.885 2.825 0.981 2.905 00 191.88804/26/2010,15:10:190 28.320.885 2.834 0.981 2.904 00 191.82504/26/2010,15:11:190 28.3180.885 2.692 0.981 2.907 00 191.904/26/2010,15:12:190 28.3150.885 2.801 0.981 2.911 00 191.93204/26/2010,15:13:190 28.3150.885 2.735 0.981 2.912 00 191.975Time:date,hh:mm:ss04/26/2010,14:23:1704/26/2010,14:24:1704/26/2010,14:25:1704/26/2010,14:26:1704/26/2010,14:27:1704/26/2010,14:28:1704/26/2010,14:29:1704/26/2010,14:30:1704/26/2010,14:31:1704/26/2010,14:32:1704/26/2010,14:33:1704/26/2010,14:34:1704/26/2010,14:35:1704/26/2010,14:36:1704/26/2010,14:37:1704/26/2010,14:38:1704/26/2010,14:39:1704/26/2010,14:40:1704/26/2010,14:41:1704/26/2010,14:42:1704/26/2010,14:43:1804/26/2010,14:44:1804/26/2010,14:45:1804/26/2010,14:46:1804/26/2010,14:47:1804/26/2010,14:48:1804/26/2010,14:49:1804/26/2010,14:50:1804/26/2010,14:51:1804/26/2010,14:52:1804/26/2010,14:53:1804/26/2010,14:54:1804/26/2010,14:55:1804/26/2010,14:56:1804/26/2010,14:57:1804/26/2010,14:58:1804/26/2010,14:59:1804/26/2010,15:00:1804/26/2010,15:01:1804/26/2010,15:02:1804/26/2010,15:03:1804/26/2010,15:04:1804/26/2010,15:05:1804/26/2010,15:06:1804/26/2010,15:07:1904/26/2010,15:08:1904/26/2010,15:09:1904/26/2010,15:10:1904/26/2010,15:11:1904/26/2010,15:12:1904/26/2010,15:13:19Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFdegF degFdegF degFdegF degF degFliters STP liters STP liters nominal liters nominal101.865 252.77980.602 81.662500 83.284 85.43189.798 443.152 424.055 479.217 469.147116.142 250.99280.667 81.614500 83.24 85.4389.791 446.253 426.959 482.569 472.36193.232 253.79480.77981.6500 83.234 85.45789.785 449.361 429.869 485.929 475.58178.57 249.95880.84 81.602500 83.262 85.57989.779 452.409 432.782 489.224 478.80578.774 252.68980.929 81.602500 83.282 85.67189.776 455.482 435.663 492.546 481.99278.304 251.30580.986 81.603500 83.293 85.6989.775 458.527 438.574 495.837 485.21478.669 250.69881.012 81.603500 83.322 85.80489.772 461.594 441.506 499.153 488.45979.323 253.1680.998 81.618500 83.339 85.76589.77 464.649 444.379 502.456 491.63979.988 249.59781.061 81.626500 83.356 85.8389.771 467.75 447.266 505.809 494.83480.376 252.57681.136 81.643500 83.387 85.90589.773 470.815 450.203 509.123 498.08481.1 250.98881.215 81.65650083.4 85.92589.773 473.868 453.073 512.424 501.26282.18 250.57181.294 81.658500 83.427 86.0389.776 476.919 455.949 515.723 504.44683.826 253.14981.413 81.667500 83.451 86.04489.776 479.973 458.876 519.026 507.68787.476 249.27981.558 81.691500 83.489 86.17489.779 483.022 461.752 522.323 510.8791.459 252.75881.658 81.712500 83.561 86.26489.785 486.109 464.616 525.662 514.04394.287 249.98481.699 81.718500 83.582 86.28589.79 489.182 467.539 528.986 517.2895.957 251.45881.791 81.815500 83.675 86.31489.797 492.218 470.411 532.269 520.46296.833 252.6181.927 81.873500 83.687 86.44889.808 495.254 473.273 535.555 523.632110.471 249.55881.963 81.884500 83.73 86.39189.814 498.307 476.189 538.858 526.863109.532 252.7981.971 81.907500 83.752 86.36489.824 501.345 479.057 542.146 530.041102.554 250.49881.978 81.934500 83.787 86.35789.834 504.434 481.918 545.488 533.212114.511 251.2281.957 81.938500 83.844 86.35489.843 507.484 484.83 548.789 536.43985.024 252.381.994 81.942500 83.895 86.48389.852 510.526 487.701 552.083 539.621216.153 249.36582.019 81.956500 83.926 86.39489.86 513.551 490.569 555.357 542.801309.561 252.66882.016 82.009500 84.005 86.46889.87 516.601 493.482 558.658 546.031299.427 250.1181.851 82.005500 84.009 86.36389.879 519.652 496.345 561.961 549.205287.552 251.18981.706 82.005500 84.01 86.43189.892 522.756 499.228 565.321 552.402276.595 252.65881.804 81.999500 84.01 86.58589.904 525.82 502.141 568.637 555.631272.53 249.83981.965 81.999500 84.005 86.66789.915 528.879 505.045 571.949 558.851274.492 253.25482.026 82.035500 84.036 86.73989.93 531.96 507.921 575.284 562.041276.702 250.59182.053 82.067500 84.067 86.85889.945 535.034 510.847 578.612 565.285275.188 252.07482.216 82.091500 84.066 86.85289.959 538.109 513.787 581.941 568.545274.342 252.78482.231 82.105500 84.069 86.83289.972 541.189 516.682 585.277 571.756275.379 250.47582.269 82.108500 84.109 86.88789.983 544.278 519.565 588.621 574.953275.153 253.68182.332 82.198500 84.205 87.01689.998 547.394 522.493 591.996 578.201274.513 250.89182.413 82.27500 84.235 87.17790.011 550.499 525.393 595.36 581.419274.869 251.70682.417 82.275500 84.236 87.23490.025 553.567 528.28 598.684 584.622274.869 252.70182.345 82.291500 84.256 87.25890.039 556.661 531.207 602.036 587.87274.486 249.7682.29 82.313500 84.277 87.20990.052 559.734 534.146 605.366 591.132274.721 252.76882.193 82.383500 84.344 86.82690.071 562.822 537.048 608.712 594.352274.687 250.1682.065 82.386500 84.348 86.59190.083 565.905 539.921 612.053 597.541274.662 251.06281.972 82.386500 84.347 86.45190.096 568.981 542.846 615.386 600.788266.211 251.64681.896 82.386500 84.345 86.30890.109 572.072 545.754 618.737 604.01581.838 249.51681.749 82.386500 84.329 86.17390.119 575.194 548.648 622.119 607.22784.133 252.77281.746 82.411500 84.324 86.27190.131 578.309 551.563 625.496 610.46387.999 249.5281.716 82.428500 84.343 86.36590.143 581.374 554.516 628.818 613.741209.158 251.82681.676 82.398500 84.312 86.21290.151 584.446 557.403 632.148 616.946140.234 251.0781.608 82.386500 84.291 85.94290.162 587.526 560.28 635.487 620.139177.479 250.2381.532 82.38500 84.28 85.9190.175 590.598 563.198 638.816 623.378231.335 252.9681.664 82.353500 84.242 85.88190.185 593.664 566.102 642.14 626.602290.195 249.25581.719 82.335500 84.235 85.68290.191 596.736 568.969 645.469 629.784Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/26/2010,15:14:190 28.3180.885 2.792 0.981 2.913 00 192.05804/26/2010,15:15:190 28.3170.885 2.826 0.981 2.91 00 192.13204/26/2010,15:16:190 28.3170.885 2.868 0.981 2.906 00 192.45904/26/2010,15:17:190 28.3210.885 2.747 0.981 2.901 00 192.72704/26/2010,15:18:190 28.3160.885 2.799 0.981 2.903 00 192.85604/26/2010,15:19:190 28.320.885 2.69 0.981 2.903 00 193.10204/26/2010,15:20:190 28.320.885 2.787 0.981 2.902 00 193.35104/26/2010,15:21:190 28.3190.885 2.834 0.981 2.903 00 193.47804/26/2010,15:22:190 28.3180.885 2.877 0.981 2.905 00 193.59304/26/2010,15:23:190 28.320.885 2.799 0.981 2.904 00 193.72904/26/2010,15:24:190 28.320.885 2.829 0.981 2.903 00 193.82604/26/2010,15:25:190 28.3180.885 2.811 0.981 2.907 00 193.7704/26/2010,15:26:190 28.3180.885 2.704 0.981 2.909 00 194.08404/26/2010,15:27:190 28.3180.885 2.829 0.981 2.896 00 194.3304/26/2010,15:28:190 28.3170.885 2.803 0.981 2.905 00 194.43304/26/2010,15:29:190 28.3180.885 2.811 0.981 2.909 00 194.53304/26/2010,15:30:190 28.3190.885 2.796 0.981 2.907 00 194.64404/26/2010,15:31:200 28.3170.885 2.76 0.981 2.904 00 194.58604/26/2010,15:32:200 28.3180.885 2.796 0.981 2.903 00 194.68704/26/2010,15:33:200 28.3190.885 2.813 0.981 2.907 00 194.78404/26/2010,15:34:200 28.3190.885 2.81 0.981 2.911 00 194.95704/26/2010,15:35:200 28.3160.885 2.822 0.981 2.908 00 194.99104/26/2010,15:36:200 28.3150.885 2.803 0.981 2.909 00 195.04804/26/2010,15:37:200 28.3120.885 2.805 0.981 2.907 00 195.51504/26/2010,15:38:200 28.3140.885 2.813 0.981 2.907 00 195.66904/26/2010,15:39:200 28.3160.885 2.819 0.981 2.91 00 195.70704/26/2010,15:40:200 28.3160.885 2.83 0.981 2.908 00 195.73404/26/2010,15:41:200 28.3180.885 2.829 0.981 2.907 00 195.75304/26/2010,15:42:200 28.3190.885 2.812 0.981 2.906 00 195.93204/26/2010,15:43:200 28.320.885 2.817 0.981 2.911 00 196.03704/26/2010,15:44:200 28.3170.885 2.82 0.981 2.91 00 196.24504/26/2010,15:45:200 28.3150.885 2.819 0.981 2.914 00 196.42604/26/2010,15:46:200 28.3140.885 2.82 0.981 2.914 00 195.62804/26/2010,15:47:200 28.3110.885 2.816 0.981 2.91 00 195.03704/26/2010,15:48:200 28.3090.885 2.818 0.981 2.91 00 195.07804/26/2010,15:49:200 28.3070.885 2.823 0.981 2.914 00 194.95504/26/2010,15:50:200 28.3070.885 2.818 0.981 2.912 00 194.47804/26/2010,15:51:200 28.3060.885 2.817 0.981 2.91 00 194.204/26/2010,15:52:200 28.3070.885 2.809 0.981 2.907 00 194.13104/26/2010,15:53:200 28.3070.885 2.815 0.981 2.911 00 194.06204/26/2010,15:54:200 28.310.885 2.806 0.981 2.907 00 193.87704/26/2010,15:55:210 28.3090.885 2.806 0.981 2.91 00 193.49304/26/2010,15:56:210 28.3080.885 2.812 0.981 2.912 00 193.31404/26/2010,15:57:210 28.3050.885 2.826 0.981 2.911 00 192.85804/26/2010,15:58:210 28.3040.885 2.82 0.981 2.915 00 192.66904/26/2010,15:59:210 28.3030.885 2.808 0.981 2.915 00 192.43904/26/2010,16:00:21 Sampling complete 239.865517 Minutes sampledC:Drive Code:0Compact Flash Code:0Time:date,hh:mm:ss04/26/2010,15:14:1904/26/2010,15:15:1904/26/2010,15:16:1904/26/2010,15:17:1904/26/2010,15:18:1904/26/2010,15:19:1904/26/2010,15:20:1904/26/2010,15:21:1904/26/2010,15:22:1904/26/2010,15:23:1904/26/2010,15:24:1904/26/2010,15:25:1904/26/2010,15:26:1904/26/2010,15:27:1904/26/2010,15:28:1904/26/2010,15:29:1904/26/2010,15:30:1904/26/2010,15:31:2004/26/2010,15:32:2004/26/2010,15:33:2004/26/2010,15:34:2004/26/2010,15:35:2004/26/2010,15:36:2004/26/2010,15:37:2004/26/2010,15:38:2004/26/2010,15:39:2004/26/2010,15:40:2004/26/2010,15:41:2004/26/2010,15:42:2004/26/2010,15:43:2004/26/2010,15:44:2004/26/2010,15:45:2004/26/2010,15:46:2004/26/2010,15:47:2004/26/2010,15:48:2004/26/2010,15:49:2004/26/2010,15:50:2004/26/2010,15:51:2004/26/2010,15:52:2004/26/2010,15:53:2004/26/2010,15:54:2004/26/2010,15:55:2104/26/2010,15:56:2104/26/2010,15:57:2104/26/2010,15:58:2104/26/2010,15:59:2104/26/2010,16:00:21C:Drive Code:0Compact Flash Code:0Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFdegF degFdegF degFdegF degF degFliters STP liters STP liters nominal liters nominal283.853 252.33181.688 82.371500 84.278 85.53290.2 599.82 571.882 648.812 633.017161.867 250.49781.632 82.362500 84.27 85.53690.211 602.926 574.823 652.179 636.282116.068 250.50381.402 82.331500 84.24 85.20390.219 606.001 577.71 655.513 639.48797.5 252.2681.376 82.296500 84.234 85.05690.225 609.063 580.591 658.831 642.684207.013 249.63381.393 82.275500 84.209 85.25490.229 612.141 583.525 662.166 645.94275.609 252.57681.38 82.255500 84.186 85.07990.235 615.218 586.418 665.501 649.151204.905 250.66581.259 82.223500 84.179 85.03690.239 618.293 589.305 668.832 652.355200.522 251.18581.199 82.193500 84.157 85.14690.244 621.367 592.222 672.164 655.592267.459 252.85881.272 82.119500 84.085 85.26790.248 624.458 595.169 675.512 658.862241.275 249.65581.27782.1500 84.065 85.55290.252 627.567 598.055 678.88 662.064277.869 253.13281.246 82.074500 84.029 85.71990.256 630.654 600.94 682.224 665.265274.912 250.76681.198 82.051500 84.011 86.00790.258 633.719 603.872 685.544 668.517271.942 251.26381.262 82.05500 84.006 86.18190.26 636.785 606.75 688.866 671.711273.448 252.71681.285 82.058500 84.003 86.28790.264 639.85 609.657 692.186 674.936275.484 249.99481.327 82.07500 84.016 86.29790.268 642.95 612.565 695.544 678.162274.288 253.40481.391 82.053500 84.013 86.28690.272 646.002 615.496 698.851 681.414273.481 250.74281.441 82.052500 84.011 86.17690.275 649.093 618.386 702.199 684.621272.681 251.61781.492 82.05500 84.012 85.84190.279 652.209 621.278 705.574 687.829272.975 252.38681.612 82.051500 84.016 85.95290.282 655.296 624.213 708.919 691.085271.666 249.88281.733 82.05500 84.011 86.12390.285 658.358 627.094 712.235 694.282272.706 253.581.873 82.05500 84.012 86.10290.289 661.44 629.997 715.574 697.502274.841 249.95581.907 82.052500 84.028 86.06590.293 664.482 632.893 718.869 700.716272.941 251.90781.99 82.072500 84.058 86.15390.295 667.581 635.817 722.227 703.961273.16 251.83982.037 82.095500 84.067 86.20390.297 670.657 638.712 725.561 707.173273.872 249.98982.041 82.105500 84.067 86.36390.302 673.728 641.606 728.888 710.385271.597 253.05382.047 82.108500 84.069 86.44490.308 676.84 644.549 732.259 713.651267.942 250.13681.997 82.118500 84.084 86.40990.314 679.941 647.434 735.619 716.852267.029 251.83281.955 82.149500 84.093 86.43490.32 682.989 650.318 738.922 720.053251.286 252.22581.875 82.151500 84.112 86.22290.327 686.076 653.234 742.267 723.288224.659 250.03781.793 82.16500 84.102 85.92290.33 689.13 656.151 745.575 726.525230.988 253.64381.729 82.222500 84.181 85.88990.335 692.206 659.035 748.909 729.726281.341 250.71581.816 82.22500 84.173 85.68490.341 695.264 661.929 752.223 732.938259.191 252.09581.681 82.218500 84.082 85.45290.345 698.343 664.872 755.56 736.203247.128 253.18981.611 82.213500 84.061 85.67290.35 701.443 667.763 758.92 739.412275.806 250.73981.626 82.187500 84.021 86.00290.355 704.512 670.631 762.246 742.596277.856 253.91981.709 82.17500 84.011 86.29290.363 707.564 673.555 765.554 745.84268.996 250.78381.767 82.167500 84.011 86.46990.367 710.613 676.437 768.859 749.039272.422 251.75381.798 82.159500 84.01 86.50490.37 713.704 679.336 772.209 752.257271.848 252.63581.862 82.157500 84.003 86.58390.374 716.779 682.232 775.543 755.471260.42 249.76781.875 82.141500 83.995 86.71790.379 719.838 685.159 778.859 758.72254.502 253.3281.909 82.155500 83.991 86.68890.384 722.94 688.048 782.22 761.926272.016 250.48681.95 82.162500 83.981 86.50690.391 726.042 690.941 785.582 765.137265.519 251.73682.005 82.167500 83.972 86.40390.399 729.094 693.877 788.891 768.395269.447 253.00982.038 82.237500 84.011 86.47490.404 732.169 696.759 792.224 771.594267.833 250.12382.04 82.247500 84.011 86.6290.409 735.21 699.632 795.521 774.783239.049 253.64382.053 82.257500 84.014 86.61790.412 738.286 702.545 798.856 778.016Hg TESTPARAMETERS 4/26/2010 10:39 AMXducerPitotBarom Flow 1Vac 1 Flow 2 Vac 2 aux LoadGain1.12 3.410.17 1100 0.189 1100 10Offset0.001 17.40.004 0.5 0.004 0.5 00TstdPstdGam 1 Gam 2CPL 2 CPL 16829.92 1.00130.9812 526.106 526.211Prop timeProbe min Filter min Stack min Test time0.5225 250150 240LpmMotor V Log Time File Suffix Load Proportion0.82.6 60 South 4-26-10 r1 Pitot ManualTime:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: Leak 1: Stack Flow:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg cc per M cc per M04/26/2010,10:39:360 28.50.824 6.658 0.889 6.518 999 99904/26/2010,10:39:520 28.5020.888 8.859 0.971 8.518 844.835 898.15904/26/2010,10:40:070 28.5010.763 10.268 0.717 9.745 1255.317 1290.98204/26/2010,10:40:220 28.4980.504 10.823 0.432 10.358 1226.378 1211.41604/26/2010,10:40:370 28.4980.355 11.342 0.297 10.757 896.979 790.71504/26/2010,10:40:520 28.4960.271 11.587 0.21 11.011 603.053 504.33404/26/2010,10:41:080 28.4960.195 11.767 0.151 11.174 392.745 331.99904/26/2010,10:41:230 28.4970.137 11.897 0.109 11.26 273.654 225.55704/26/2010,10:41:380 28.4950.108 11.843 0.092 11.308 164.699 157.12904/26/2010,10:41:530 28.4950.094 11.952 0.073 11.337 88.684 93.77104/26/2010,10:42:080 28.4940.087 11.891 0.064 11.36 35.474 65.89304/26/2010,10:42:240 28.4920.084 11.983 0.066 11.374 30.406 35.48104/26/2010,10:42:390 28.4960.083 11.92 0.072 11.384 15.203 20.27504/26/2010,10:42:540 28.4920.082 11.9 0.06 11.39 7.602 12.67204/26/2010,10:43:090 28.4910.561 9.263 0.049 11.385 7.602 7.60304/26/2010,10:43:240 28.4950.888 6.129 0.054 11.383 349.67 7.60304/26/2010,10:43:400 28.4880.888 7.981 0.052 11.378 1102.219 5.06904/26/2010,10:43:550 28.4890.858 9.623 0.054 11.39 1707.807 2.53404/26/2010,10:44:100 28.4890.594 10.767 0.057 11.395 1662.198 2.53404/26/2010,10:44:250 28.4890.402 11.285 0.056 11.398 1145.295 2.53404/26/2010,10:44:400 28.4880.295 11.601 0.058 11.401 663.866 5.06904/26/2010,10:44:560 28.4860.2 11.724 0.056 11.409 458.625 2.534Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/26/2010,10:39:3604/26/2010,10:39:5204/26/2010,10:40:0704/26/2010,10:40:2204/26/2010,10:40:3704/26/2010,10:40:5204/26/2010,10:41:0804/26/2010,10:41:2304/26/2010,10:41:3804/26/2010,10:41:5304/26/2010,10:42:0804/26/2010,10:42:2404/26/2010,10:42:3904/26/2010,10:42:5404/26/2010,10:43:0904/26/2010,10:43:2404/26/2010,10:43:4004/26/2010,10:43:5504/26/2010,10:44:1004/26/2010,10:44:2504/26/2010,10:44:4004/26/2010,10:44:56Stack Temp: Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp:degF degFdegF degFdegFdegFdegF86.099 123.743 214.00373.928 72.607500 74.1686.321 126.997 220.72874.913 73.421500 74.77587.594 130.244 226.90475.415 73.88500 74.82887.812 133.466 232.04874.158 72.641500 74.26189.776 137.077 237.42174.8 73.361500 74.4189.986 139.862 243.16474.294 72.703500 74.32890.391 142.956 247.9274.326 72.716500 74.34491.006 146.039 249.18274.369 72.71500 74.36291.569 149.137 246.9374.466 72.803500 74.43491.882 152.201 242.9974.578 72.846500 74.49692.125 155.197 240.43774.648 72.852500 74.51791.976 158.177 240.85574.77 72.874500 74.56491.429 161.035 243.86274.825 72.917500 74.59890.867 163.838 247.174.857 72.917500 74.61590.537 166.632 247.64774.922 72.946500 74.69990.344 169.405 245.30775.04 72.977500 74.75795.85 172.121 242.77875.046 72.977500 74.76691.493 174.814 242.68775.137 73.027500 74.84192.306 177.443 245.1975.168 73.029500 74.86993.454 180.016 247.56475.215 73.08500 74.90794.383 182.614 247.22775.279 73.154500 75.00595.046 185.193 244.8975.359 73.161500 75.037Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/26/2010,10:39:3604/26/2010,10:39:5204/26/2010,10:40:0704/26/2010,10:40:2204/26/2010,10:40:3704/26/2010,10:40:5204/26/2010,10:41:0804/26/2010,10:41:2304/26/2010,10:41:3804/26/2010,10:41:5304/26/2010,10:42:0804/26/2010,10:42:2404/26/2010,10:42:3904/26/2010,10:42:5404/26/2010,10:43:0904/26/2010,10:43:2404/26/2010,10:43:4004/26/2010,10:43:5504/26/2010,10:44:1004/26/2010,10:44:2504/26/2010,10:44:4004/26/2010,10:44:56AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degF degFliters STP liters STP liters nominal liters nominal72.6970.101 0.363 0.392 0.384 0.42472.43670.123 0.654 0.663 0.692 0.71872.58570.145 0.869 0.839 0.92 0.90972.90970.157 0.998 0.939 1.057 1.01772.82170.188 1.081 1.013 1.144 1.09773.03370.198 1.147 1.069 1.214 1.15873.07670.217 1.192 1.095 1.262 1.18673.14170.237 1.198 1.121 1.268 1.21573.21270.259 1.21 1.134 1.281 1.22873.26870.28 1.217 1.141 1.288 1.23573.3370.302 1.219 1.146 1.29 1.24173.4470.325 1.221 1.148 1.292 1.24373.5470.345 1.223 1.149 1.294 1.24573.59570.369 1.225 1.151 1.296 1.24773.72570.395 1.469 1.153 1.555 1.24973.87570.417 2.004 1.153 2.121 1.24973.92570.444 2.434 1.153 2.577 1.24974.01870.47 2.646 1.155 2.801 1.25174.13270.496 2.815 1.155 2.98 1.25174.1670.524 2.905 1.156 3.075 1.25374.23570.55 2.971 1.156 3.145 1.25374.26170.582 3.011 1.158 3.187 1.25504/26/2010,10:45:110 28.4850.129 11.951 0.057 11.425 276.188 5.06904/26/2010,10:45:260 28.4880.099 11.932 0.057 11.423 179.902 2.53404/26/2010,10:45:410 28.4870.088 11.93 0.062 11.428 93.752 5.06904/26/2010,10:45:570 28.4870.084 12.012 0.052 11.426 40.541 5.06904/26/2010,10:46:120 28.4860.084 11.977 0.052 11.437 15.203 5.06904/26/2010,10:46:270 28.4860.081 12.009 0.059 11.439 10.135 2.53404/26/2010,10:46:420 28.4840.081 11.96 0.051 11.439 7.602 2.53404/26/2010,10:46:570 28.4830.082 11.986 0.051 11.442 5.068 2.53404/26/2010,10:47:130 28.4810.08 11.954 0.053 11.447 5.068 2.53404/26/2010,10:47:280 28.4840.081 12.013 0.054 11.452 5.068 2.53404/26/2010,10:47:430 28.4830.08 12.013 0.053 11.454 5.068 2.53404/26/2010,10:47:580 28.4790.079 12.079 0.045 11.459 5.068 2.53404/26/2010,10:48:130 28.4760.079 11.993 0.055 11.462 5.068 2.53404/26/2010,10:48:290 28.4780.081 11.931 0.056 11.462 5.068 2.53404/26/2010,10:48:440 28.4780.081 11.969 0.052 11.464 5.068 2.53404/26/2010,10:48:590 28.4750.082 12.004 0.056 11.466 5.068004/26/2010,10:49:140 28.4750.079 11.966 0.052 11.47 5.068 2.53404/26/2010,10:49:290 28.4740.082 12 0.052 11.47 2.534 2.53404/26/2010,10:49:450 28.4720.082 11.97 0.051 11.469 5.068 2.53404/26/2010,10:50:000 28.4760.081 11.98 0.052 11.477 5.068004/26/2010,10:50:150 28.4760.138 11.957 0.081 11.426 5.068 2.53404/26/2010,10:50:300 28.4720.114 11.922 0.106 11.403 38.008 7.60304/26/2010,10:50:460 28.4710.09 11.993 0.084 11.45 50.677 20.27504/26/2010,10:51:010 28.4720.084 11.968 0.064 11.463 53.211 25.34304/26/2010,10:51:160 28.4730.082 12.022 0.06 11.469 20.271 22.80904/26/2010,10:51:310 28.470.083 12.013 0.055 11.474 7.602 12.67204/26/2010,10:51:460 28.470.082 11.957 0.052 11.47 5.068 7.60304/26/2010,10:52:020 28.4720.083 12.011 0.055 11.482 5.068 7.60304/26/2010,10:52:170 28.470.084 12.027 0.053 11.483 5.068 5.06904/26/2010,10:52:320 28.4720.083 11.953 0.052 11.483 5.068 5.06904/26/2010,10:52:470 28.4740.083 11.995 0.056 11.482 7.602 2.53404/26/2010,10:53:020 28.4760.085 12.005 0.06 11.486 7.602 5.06904/26/2010,10:53:180 28.4770.085 12.011 0.061 11.49 10.135 2.53404/26/2010,10:53:330 28.4750.086 11.996 0.052 11.49 7.602 2.53404/26/2010,10:53:480 28.4720.085 11.964 0.05 11.49 10.135 2.53404/26/2010,10:54:030 28.4730.085 12.051 0.054 11.489 10.135 2.53404/26/2010,10:54:180 28.4720.085 12.032 0.056 11.494 10.135 2.53404/26/2010,10:45:1104/26/2010,10:45:2604/26/2010,10:45:4104/26/2010,10:45:5704/26/2010,10:46:1204/26/2010,10:46:2704/26/2010,10:46:4204/26/2010,10:46:5704/26/2010,10:47:1304/26/2010,10:47:2804/26/2010,10:47:4304/26/2010,10:47:5804/26/2010,10:48:1304/26/2010,10:48:2904/26/2010,10:48:4404/26/2010,10:48:5904/26/2010,10:49:1404/26/2010,10:49:2904/26/2010,10:49:4504/26/2010,10:50:0004/26/2010,10:50:1504/26/2010,10:50:3004/26/2010,10:50:4604/26/2010,10:51:0104/26/2010,10:51:1604/26/2010,10:51:3104/26/2010,10:51:4604/26/2010,10:52:0204/26/2010,10:52:1704/26/2010,10:52:3204/26/2010,10:52:4704/26/2010,10:53:0204/26/2010,10:53:1804/26/2010,10:53:3304/26/2010,10:53:4804/26/2010,10:54:0304/26/2010,10:54:1895.596 187.75 243.2575.431 73.206500 75.09896.529 190.183 244.2175.447 73.22500 75.12197.06 192.682 247.39875.513 73.26500 75.1897.541 195.121 249.39475.553 73.291500 75.21497.936 197.562 248.45375.618 73.312500 75.27998.302 199.998 245.16275.695 73.346500 75.37398.62 202.327 242.97375.723 73.359500 75.38899.141 204.667 244.23975.774 73.477500 75.45499.445 206.97 247.71975.788 73.471500 75.49198.824 209.238 250.21475.87 73.52500 75.53798.212 211.449 249.66875.9 73.533500 75.56397.572 213.693 246.85975.97 73.568500 75.65296.596 215.907 244.14976.01 73.589500 75.71895.962 218.054 244.14676.081 73.62500 75.74995.997 220.106 246.77776.161 73.645500 75.78896.322 222.092 249.74476.186 73.669500 75.84496.42 224.118 250.50776.228 73.71500 75.89196.065 226.106 248.44976.279 73.813500 75.9695.696 228.083 245.30776.299 73.822500 76.0195.419 230.035 244.27276.391 73.869500 76.11194.897 231.904 246.29976.428 73.883500 76.12494.925 233.75 249.71476.507 73.939500 76.18195.03 235.537 251.35876.522 73.947500 76.22695.14 237.305 249.95376.559 73.981500 76.27195.627 239.07 246.58276.578 74.009500 76.31495.659 240.87 244.35776.615 74.046500 76.39195.845 242.569 245.23876.68 74.113500 76.44895.99 244.264 248.32476.731 74.163500 76.47896.161 245.969 251.10976.776 74.198500 76.54396.329 247.628 251.49876.786 74.205500 76.55995.63 249.287 248.93776.832 74.269500 76.62194.753 250.895 245.48276.845 74.292500 76.65393.859 252.499 244.74576.886 74.331500 76.77892.955 254.023 246.95476.91 74.34500 76.80192.194 255.54 250.30276.947 74.379500 76.83991.695 257.047 251.72177.004 74.453500 76.87191.152 258.555 250.69877.063 74.494500 76.92304/26/2010,10:45:1104/26/2010,10:45:2604/26/2010,10:45:4104/26/2010,10:45:5704/26/2010,10:46:1204/26/2010,10:46:2704/26/2010,10:46:4204/26/2010,10:46:5704/26/2010,10:47:1304/26/2010,10:47:2804/26/2010,10:47:4304/26/2010,10:47:5804/26/2010,10:48:1304/26/2010,10:48:2904/26/2010,10:48:4404/26/2010,10:48:5904/26/2010,10:49:1404/26/2010,10:49:2904/26/2010,10:49:4504/26/2010,10:50:0004/26/2010,10:50:1504/26/2010,10:50:3004/26/2010,10:50:4604/26/2010,10:51:0104/26/2010,10:51:1604/26/2010,10:51:3104/26/2010,10:51:4604/26/2010,10:52:0204/26/2010,10:52:1704/26/2010,10:52:3204/26/2010,10:52:4704/26/2010,10:53:0204/26/2010,10:53:1804/26/2010,10:53:3304/26/2010,10:53:4804/26/2010,10:54:0304/26/2010,10:54:1874.326 70.61 3.032 1.158 3.21 1.25574.38270.639 3.037 1.16 3.215 1.25674.48970.669 3.039 1.162 3.217 1.25874.55870.697 3.043 1.162 3.221 1.25874.61870.731 3.045 1.162 3.223 1.25874.7170.76 3.045 1.163 3.223 1.2674.72970.792 3.046 1.163 3.225 1.2674.81770.822 3.048 1.163 3.227 1.2674.83770.854 3.048 1.165 3.227 1.26274.91970.887 3.05 1.165 3.229 1.26274.94370.914 3.052 1.165 3.231 1.26275.04670.947 3.052 1.167 3.231 1.26475.10570.98 3.054 1.167 3.233 1.26475.13671.012 3.055 1.167 3.234 1.26475.20171.046 3.055 1.167 3.234 1.26475.24571.08 3.057 1.169 3.236 1.26675.36171.118 3.057 1.169 3.236 1.26675.45171.151 3.059 1.169 3.238 1.26675.51371.186 3.061 1.169 3.24 1.26675.62471.221 3.061 1.17 3.24 1.26875.68371.256 3.086 1.174 3.267 1.27275.7771.292 3.097 1.183 3.278 1.28175.83871.326 3.098 1.188 3.28 1.28775.89471.364 3.1 1.19 3.282 1.28975.96771.398 3.102 1.191 3.284 1.29176.04471.435 3.102 1.193 3.284 1.29376.11871.471 3.104 1.195 3.286 1.29476.16771.507 3.106 1.195 3.288 1.29476.20571.547 3.106 1.197 3.288 1.29676.24871.582 3.109 1.197 3.291 1.29676.35771.621 3.111 1.198 3.293 1.29876.39471.657 3.113 1.198 3.295 1.29876.49471.694 3.114 1.198 3.297 1.29876.52871.734 3.118 1.2 3.3011.376.59771.77 3.12 1.2 3.3031.376.66571.81 3.122 1.2 3.3051.376.70371.851 3.123 1.202 3.307 1.30204/26/2010,10:54:340 28.4710.085 12.133 0.056 11.486 7.602 2.53404/26/2010,10:54:38 Sampling terminated byoperator 15.166167 Minutes sampledC:Drive Code:0Compact Flash Code:0Hg TESTPARAMETERS 4/26/2010 4:10 PMXducerPitotBarom Flow 1Vac 1 Flow 2 Vac 2 aux LoadGain1.12 3.410.17 1100 0.189 1100 10Offset0.001 17.40.004 0.5 0.004 0.5 00TstdPstdGam 1 Gam 2CPL 2 CPL 16829.92 1.00130.9812 526.106 526.211Prop timeProbe min Filter min Stack min Test time0.5225 250150 240LpmMotor V Log Time File Suffix Load Proportion0.82.6 60 South 4-26-10 r1 Pitot ManualTime:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: Leak 1: Stack Flow:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg cc per M cc per M04/26/2010,16:10:390 28.2960.825 6.735 0.886 6.553 7.602 2.53404/26/2010,16:10:540 28.2960.888 8.582 0.968 8.529 875.241 926.03604/26/2010,16:11:090 28.2950.76 10.112 0.685 9.68 1361.738 1334.06604/26/2010,16:11:240 28.2940.494 10.633 0.398 10.314 1277.054 1272.2404/26/2010,16:11:400 28.2940.371 11.347 0.292 10.734 894.445 854.07404/26/2010,16:11:550 28.2940.261 11.496 0.197 11.013 562.512 504.33404/26/2010,16:12:100 28.2940.183 11.489 0.129 11.164 367.406 281.31204/26/2010,16:12:250 28.2940.138 11.836 0.086 11.253 258.451 149.52604/26/2010,16:12:400 28.2940.118 11.81 0.066 11.298 121.624 93.77104/26/2010,16:12:560 28.2930.108 11.859 0.054 11.329 81.083 70.96204/26/2010,16:13:110 28.2940.105 11.813 0.046 11.343 38.008 40.54904/26/2010,16:13:260 28.2960.104 12.01 0.041 11.358 20.271 40.54904/26/2010,16:13:410 28.2950.103 11.797 0.043 11.362 12.669 20.27504/26/2010,16:13:560 28.2950.101 12.089 0.042 11.373 10.135 12.67204/26/2010,16:14:120 28.2950.1 11.909 0.041 11.379 10.135 12.67204/26/2010,16:14:270 28.2950.101 11.85 0.034 11.381 7.602 10.13704/26/2010,16:14:420 28.2940.099 11.83 0.035 11.39 5.068 10.13704/26/2010,16:14:570 28.2920.1 11.981 0.037 11.393 5.068 7.60304/26/2010,10:54:3404/26/2010,10:54:38C:Drive Code:0Compact Flash Code:0Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/26/2010,16:10:3904/26/2010,16:10:5404/26/2010,16:11:0904/26/2010,16:11:2404/26/2010,16:11:4004/26/2010,16:11:5504/26/2010,16:12:1004/26/2010,16:12:2504/26/2010,16:12:4004/26/2010,16:12:5604/26/2010,16:13:1104/26/2010,16:13:2604/26/2010,16:13:4104/26/2010,16:13:5604/26/2010,16:14:1204/26/2010,16:14:2704/26/2010,16:14:4204/26/2010,16:14:5790.943 259.546 248.94677.078 74.511500 76.936Stack Temp: Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp:degF degFdegF degFdegFdegFdegF112.622 277.026 252.65982.74 82.554500 84.291111.673 275.539 255.44682.722 82.554500 84.316111.124 274.635 255.64882.681 82.554500 84.329110.126 274.197 253.14882.666 82.576500 84.347108.297 274.178 250.28582.707 82.566500 84.363108.349 274.464 250.01282.744 82.564500 84.393109.325 274.981 252.47482.774 82.573500 84.403110.146 275.698 255.2882.825 82.601500 84.456110.236 276.472 255.54782.876 82.598500 84.515109.936 277.106 253.1782.895 82.61500 84.524109.639 277.439 250.46382.89 82.61500 84.534109.666 277.429 250.32282.89 82.61500 84.571109.713 277.094 252.82882.89 82.61500 84.571109.557 276.55 255.35382.89 82.626500 84.598109.754 275.947 255.25282.901 82.619500 84.627109.943 275.398 252.70182.943 82.615500 84.627110.079 275.027 250.25182.985 82.64500 84.632109.335 274.791 250.49783.048 82.659500 84.67604/26/2010,10:54:3404/26/2010,10:54:38C:Drive Code:0Compact Flash Code:0Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/26/2010,16:10:3904/26/2010,16:10:5404/26/2010,16:11:0904/26/2010,16:11:2404/26/2010,16:11:4004/26/2010,16:11:5504/26/2010,16:12:1004/26/2010,16:12:2504/26/2010,16:12:4004/26/2010,16:12:5604/26/2010,16:13:1104/26/2010,16:13:2604/26/2010,16:13:4104/26/2010,16:13:5604/26/2010,16:14:1204/26/2010,16:14:2704/26/2010,16:14:4204/26/2010,16:14:5776.666 71.874 3.125 1.202 3.309 1.302AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degF degF liters STP liters STP liters nominal liters nominal87.054 90.485 0.373 0.399 0.405 0.44387.042 90.485 0.711 0.676 0.772 0.75187.169 90.487 0.883 0.859 0.958 0.95487.174 90.489 0.991 0.975 1.076 1.08387.199 90.492 1.1 1.016 1.193 1.12987.29 90.496 1.137 1.049 1.233 1.16587.34 90.497 1.17 1.076 1.269 1.19687.371 90.5 1.184 1.08 1.285 1.19987.336 90.503 1.193 1.097 1.294 1.21887.337 90.506 1.196 1.104 1.298 1.22687.368 90.509 1.198 1.107 1.3 1.2387.451 90.512 1.201 1.11 1.304 1.23487.526 90.516 1.203 1.112 1.306 1.23587.55 90.519 1.205 1.115 1.307 1.23987.62 90.522 1.207 1.117 1.309 1.24187.641 90.525 1.207 1.119 1.309 1.24387.668 90.529 1.208 1.121 1.311 1.24587.75 90.532 1.21 1.121 1.313 1.245Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: Leak 1: Stack Flow:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg cc per M cc per M04/26/2010,16:15:130 28.2930.101 11.852 0.031 11.396 5.068 5.06904/26/2010,16:15:280 28.290.099 11.988 0.03 11.388 7.602 5.06904/26/2010,16:15:430 28.2860.097 11.493 0.038 11.398 7.602 2.53404/26/2010,16:15:52 Sampling terminated byoperator 5.231967 Minutes sampledC:Drive Code:0Compact Flash Code:0Time:date,hh:mm:ss04/26/2010,16:15:1304/26/2010,16:15:2804/26/2010,16:15:4304/26/2010,16:15:52C:Drive Code:0Compact Flash Code:0Stack Temp: Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp:degF degFdegF degFdegFdegFdegF108.84 274.866 253.27583.101 82.712500 84.73108.237 275.005 255.52283.097 82.719500 84.739107.628 275.151 255.43683.076 82.722500 84.755Time:date,hh:mm:ss04/26/2010,16:15:1304/26/2010,16:15:2804/26/2010,16:15:4304/26/2010,16:15:52C:Drive Code:0Compact Flash Code:0AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degF degFliters STP liters STP liters nominal liters nominal87.77490.536 1.212 1.122 1.315 1.24787.74690.54 1.214 1.122 1.317 1.24787.71990.544 1.215 1.124 1.319 1.249Hg TESTPARAMETERS 4/27/2010 9:00 AMXducerPitotBarom Flow 1Vac 1 Flow 2 Vac 2 aux LoadGain1.12 3.410.17 1100 0.189 1100 10Offset0.001 17.40.004 0.5 0.004 0.5 00TstdPstdGam 1 Gam 2CPL 2 CPL 16829.92 1.00130.9812 526.106 526.211Prop timeProbe min Filter min Stack min Test time0.5225 250150 240LpmMotor V Log Time File Suffix Load Proportion0.82.6 60 South 4-27-10 r2 Pitot ManualTime:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,09:00:320 28.7580.773 3.588 0.659 3.486 00 190.7604/27/2010,09:01:320 28.7590.888 2.797 0.987 2.919 00 190.78704/27/2010,09:02:320 28.7590.888 2.772 0.987 2.882 00 191.12804/27/2010,09:03:320 28.7580.888 2.765 0.987 2.876 00 191.45204/27/2010,09:04:330 28.7590.888 2.781 0.987 2.872 00 191.56104/27/2010,09:05:330 28.7610.888 2.783 0.987 2.869 00 191.47704/27/2010,09:06:330 28.7640.888 2.769 0.987 2.865 00 191.35804/27/2010,09:07:330 28.7660.888 2.741 0.987 2.863 00 191.18104/27/2010,09:08:330 28.7670.888 2.765 0.987 2.859 00 191.14804/27/2010,09:09:330 28.7680.888 2.738 0.987 2.855 00 191.14204/27/2010,09:10:330 28.7680.888 2.782 0.987 2.858 00 191.4804/27/2010,09:11:330 28.770.888 2.742 0.987 2.856 00 191.25904/27/2010,09:12:330 28.7680.888 2.662 0.986 2.852 00 190.8104/27/2010,09:13:330 28.7670.888 2.877 0.986 2.856 00 191.00504/27/2010,09:14:330 28.7670.888 2.784 0.986 2.855 00 191.03604/27/2010,09:15:330 28.7650.888 2.821 0.986 2.857 00 191.10204/27/2010,09:16:330 28.7630.888 2.741 0.986 2.859 00 191.01204/27/2010,09:17:330 28.7640.888 2.725 0.986 2.858 00 191.18504/27/2010,09:18:330 28.7610.888 2.781 0.986 2.861 00 191.35504/27/2010,09:19:330 28.7590.888 2.749 0.986 2.864 00 191.58904/27/2010,09:20:330 28.7570.888 2.744 0.986 2.859 00 191.69504/27/2010,09:21:330 28.7590.888 2.806 0.986 2.86 00 191.823Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,09:00:3204/27/2010,09:01:3204/27/2010,09:02:3204/27/2010,09:03:3204/27/2010,09:04:3304/27/2010,09:05:3304/27/2010,09:06:3304/27/2010,09:07:3304/27/2010,09:08:3304/27/2010,09:09:3304/27/2010,09:10:3304/27/2010,09:11:3304/27/2010,09:12:3304/27/2010,09:13:3304/27/2010,09:14:3304/27/2010,09:15:3304/27/2010,09:16:3304/27/2010,09:17:3304/27/2010,09:18:3304/27/2010,09:19:3304/27/2010,09:20:3304/27/2010,09:21:33Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF64.307 250.12566.556 65.333500 67.283 71.58364.477 251.54166.631 65.402500 67.352 71.61965.016 251.36966.731 65.407500 67.369 71.618230.876 250.21566.861 65.514500 67.476 71.71309.87 252.01366.869 65.56500 67.533 71.826298.789 251.05466.874 65.586500 67.548 71.916286.335 250.68266.937 65.636500 67.614 72.076275.72 252.42466.973 65.667500 67.64 72.214272.881 249.85167.025 65.731500 67.738 72.309274.961 251.53367.056 65.753500 67.782 72.28277.494 251.45867.18 65.849500 67.842 72.268276.467 250.21567.257 65.913500 67.877 72.333275.661 252.19167.327 65.937500 67.939 72.418276.457 250.81967.432 66.017500 68.043 72.54276.358 250.44167.405 66.029500 68.081 72.429275.853 252.44867.597 66.15500 68.154 72.504275.968 249.39367.589 66.194500 68.191 72.436276.056 251.8367.687 66.268500 68.262 72.391275.822 251.26867.808 66.30450068.3 72.489275.731 249.83367.953 66.404500 68.427 72.613275.817 252.31668.052 66.467500 68.449 72.643275.704 250.0568.173 66.544500 68.541 72.837Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,09:00:3204/27/2010,09:01:3204/27/2010,09:02:3204/27/2010,09:03:3204/27/2010,09:04:3304/27/2010,09:05:3304/27/2010,09:06:3304/27/2010,09:07:3304/27/2010,09:08:3304/27/2010,09:09:3304/27/2010,09:10:3304/27/2010,09:11:3304/27/2010,09:12:3304/27/2010,09:13:3304/27/2010,09:14:3304/27/2010,09:15:3304/27/2010,09:16:3304/27/2010,09:17:3304/27/2010,09:18:3304/27/2010,09:19:3304/27/2010,09:20:3304/27/2010,09:21:33Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal73.569 2.502 2.177 2.586 2.30673.593 5.683 5.225 5.876 5.53373.619 8.948 8.26 9.251 8.74773.643 12.206 11.291 12.62 11.95873.669 15.425 14.371 15.95 15.22173.696 18.657 17.427 19.293 18.45873.726 21.91 20.476 22.656 21.68873.755 25.14 23.546 25.997 24.9473.782 28.413 26.64 29.382 28.21973.811 31.676 29.712 32.757 31.47373.841 34.935 32.784 36.128 34.72973.871 38.192 35.844 39.497 37.97173.902 41.465 38.931 42.884 41.24373.934 44.723 42.029 46.255 44.52773.965 48.001 45.106 49.647 47.78973.996 51.283 48.142 53.045 51.00974.028 54.558 51.218 56.436 54.2774.061 57.823 54.327 59.816 57.56874.095 61.073 57.38 63.182 60.80774.128 64.32 60.427 66.546 64.0474.163 67.574 63.493 69.917 67.29474.198 70.844 66.604 73.305 70.596Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,09:22:330 28.7610.888 2.745 0.986 2.857 00 191.52804/27/2010,09:23:330 28.7620.888 2.724 0.986 2.86 00 191.42804/27/2010,09:24:330 28.7610.888 2.738 0.986 2.86 00 191.2404/27/2010,09:25:330 28.7590.888 2.705 0.986 2.861 00 191.35804/27/2010,09:26:330 28.7620.888 2.976 0.985 2.858 00 191.32104/27/2010,09:27:330 28.7650.888 3.066 0.985 2.854 00 191.27804/27/2010,09:28:330 28.7680.888 2.688 0.985 2.856 00 191.2904/27/2010,09:29:340 28.7670.888 2.626 0.985 2.859 00 191.29704/27/2010,09:30:340 28.7680.888 2.635 0.985 2.856 00 191.39304/27/2010,09:31:340 28.7710.888 2.716 0.985 2.853 00 191.5104/27/2010,09:32:340 28.7730.888 2.809 0.985 2.855 00 191.58104/27/2010,09:33:340 28.7750.888 2.544 0.985 2.855 00 191.45604/27/2010,09:34:340 28.7760.888 2.7 0.985 2.858 00 191.2704/27/2010,09:35:340 28.7760.888 2.799 0.985 2.855 00 191.13804/27/2010,09:36:340 28.7770.888 2.966 0.985 2.858 00 191.01104/27/2010,09:37:340 28.7790.888 2.564 0.985 2.862 00 191.02204/27/2010,09:38:340 28.7760.888 2.635 0.985 2.862 00 190.96104/27/2010,09:39:340 28.780.888 2.804 0.985 2.856 00 190.96104/27/2010,09:40:340 28.780.888 2.683 0.985 2.855 00 190.98704/27/2010,09:41:340 28.780.888 2.818 0.985 2.852 00 191.01404/27/2010,09:42:340 28.7770.888 2.792 0.985 2.854 00 191.1704/27/2010,09:43:340 28.7790.888 2.753 0.985 2.848 00 191.14104/27/2010,09:44:340 28.7820.888 2.846 0.985 2.853 00 191.23104/27/2010,09:45:340 28.7840.888 2.75 0.985 2.854 00 191.50504/27/2010,09:46:340 28.7830.888 2.742 0.985 2.851 00 191.74204/27/2010,09:47:340 28.7850.888 2.754 0.985 2.853 00 191.75304/27/2010,09:48:340 28.7840.888 2.751 0.985 2.849 00 191.84404/27/2010,09:49:340 28.7850.888 2.772 0.985 2.85 00 191.88904/27/2010,09:50:340 28.7850.888 2.663 0.985 2.85 00 191.96304/27/2010,09:51:340 28.7860.888 2.737 0.985 2.857 00 191.98504/27/2010,09:52:340 28.7850.888 2.798 0.985 2.854 00 192.25204/27/2010,09:53:350 28.7860.888 2.615 0.985 2.852 00 192.32704/27/2010,09:54:350 28.7890.888 2.861 0.985 2.852 00 192.31204/27/2010,09:55:350 28.790.888 2.804 0.985 2.852 00 192.62504/27/2010,09:56:350 28.7920.888 2.807 0.985 2.852 00 192.639Time:date,hh:mm:ss04/27/2010,09:22:3304/27/2010,09:23:3304/27/2010,09:24:3304/27/2010,09:25:3304/27/2010,09:26:3304/27/2010,09:27:3304/27/2010,09:28:3304/27/2010,09:29:3404/27/2010,09:30:3404/27/2010,09:31:3404/27/2010,09:32:3404/27/2010,09:33:3404/27/2010,09:34:3404/27/2010,09:35:3404/27/2010,09:36:3404/27/2010,09:37:3404/27/2010,09:38:3404/27/2010,09:39:3404/27/2010,09:40:3404/27/2010,09:41:3404/27/2010,09:42:3404/27/2010,09:43:3404/27/2010,09:44:3404/27/2010,09:45:3404/27/2010,09:46:3404/27/2010,09:47:3404/27/2010,09:48:3404/27/2010,09:49:3404/27/2010,09:50:3404/27/2010,09:51:3404/27/2010,09:52:3404/27/2010,09:53:3504/27/2010,09:54:3504/27/2010,09:55:3504/27/2010,09:56:35Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF275.54 251.24868.217 66.584500 68.592 72.922275.602 252.10768.4 66.663500 68.717 73.062275.531 249.77368.473 66.717500 68.765 73.075275.292 251.81668.433 66.83500 68.833 72.837275.107 250.28868.377 66.885500 68.913 72.938275.164 250.49468.387 66.928500 68.995 73.021275.126 252.02168.483 66.987500 69.058 73.033275.076 249.69968.519 67.033500 69.104 73.223275.039 251.23168.494 67.142500 69.169 73.501274.844 250.87368.429 67.182500 69.21 73.393274.936 249.83268.472 67.242500 69.301 73.348275.039 252.168.564 67.295500 69.365 73.38274.887 250.06668.646 67.311500 69.387 73.529274.827 250.96568.758 67.366500 69.441 73.579274.901 252.24368.789 67.406500 69.479 73.656274.742 249.72968.871 67.494500 69.547 73.66274.696 251.93768.881 67.567500 69.636 73.584274.507 249.08168.825 67.599500 69.675 73.503274.351 250.56168.841 67.648500 69.727 73.658274.555 250.98368.801 67.713500 69.762 73.759274.562 249.23468.724 67.76500 69.78 73.85274.358 251.58168.707 67.81500 69.833 73.849274.393 250.21968.687 67.823500 69.873 73.839274.648 250.55468.635 67.84500 69.929 73.876274.495 251.29368.522 67.86500 69.941 73.906274.212 249.25868.421 67.872500 69.951 73.731274.364 251.5868.383 67.89250070 73.654274.6 250.7768.501 67.894500 69.98 73.649274.354 250.29168.479 67.906500 70.005 73.692274.215 252.23268.524 67.914500 70.03 73.708274.482 250.33168.59 67.93500 70.029 73.858274.489 250.98468.536 67.998500 70.061 73.922274.111 250.92968.427 67.966500 70.07 73.813274.3 250.0568.485 68.034500 70.094 73.938274.478 251.9968.449 68.01500 70.083 73.911Time:date,hh:mm:ss04/27/2010,09:22:3304/27/2010,09:23:3304/27/2010,09:24:3304/27/2010,09:25:3304/27/2010,09:26:3304/27/2010,09:27:3304/27/2010,09:28:3304/27/2010,09:29:3404/27/2010,09:30:3404/27/2010,09:31:3404/27/2010,09:32:3404/27/2010,09:33:3404/27/2010,09:34:3404/27/2010,09:35:3404/27/2010,09:36:3404/27/2010,09:37:3404/27/2010,09:38:3404/27/2010,09:39:3404/27/2010,09:40:3404/27/2010,09:41:3404/27/2010,09:42:3404/27/2010,09:43:3404/27/2010,09:44:3404/27/2010,09:45:3404/27/2010,09:46:3404/27/2010,09:47:3404/27/2010,09:48:3404/27/2010,09:49:3404/27/2010,09:50:3404/27/2010,09:51:3404/27/2010,09:52:3404/27/2010,09:53:3504/27/2010,09:54:3504/27/2010,09:55:3504/27/2010,09:56:35Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal74.233 74.09 69.637 76.669 73.81674.269 77.332 72.692 80.029 77.05974.306 80.611 75.76 83.427 80.31774.344 83.857 78.867 86.792 83.61674.38 87.113 81.904 90.167 86.84274.418 90.37 84.958 93.544 90.08574.457 93.624 88.038 96.917 93.35674.496 96.888 91.13 100.302 96.6474.537 100.167 94.187 103.702 99.88974.577 103.445 97.254 107.102 103.14774.621 106.727 100.316 110.505 106.39974.663 110.006 103.394 113.905 109.6774.703 113.273 106.484 117.293 112.95374.743 116.522 109.554 120.663 116.21474.783 119.772 112.588 124.034 119.43874.828 123.015 115.652 127.398 122.69474.87 126.291 118.754 130.797 125.99274.912 129.55 121.807 134.178 129.23674.954 132.799 124.861 137.549 132.48374.995 136.061 127.931 140.934 135.74675.038 139.326 131.038 144.322 139.0575.08 142.614 134.091 147.735 142.29675.123 145.879 137.155 151.124 145.55475.166 149.144 140.221 154.512 148.81475.207 152.405 143.305 157.897 152.09375.249 155.677 146.406 161.293 155.39175.29 158.94 149.477 164.679 158.65675.328 162.212 152.53 168.075 161.90375.368 165.476 155.6 171.464 165.16675.408 168.748 158.706 174.86 168.4775.448 172.026 161.75 178.261 171.70775.488 175.305 164.815 181.665 174.96775.526 178.582 167.89 185.066 178.23675.562 181.861 170.975 188.47 181.51775.598 185.139 174.078 191.872 184.816Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,09:57:350 28.7950.888 2.7 0.985 2.849 00 192.62504/27/2010,09:58:350 28.7940.888 2.5 0.985 2.853 00 192.7304/27/2010,09:59:350 28.7950.888 2.71 0.985 2.852 00 192.8504/27/2010,10:00:350 28.7950.888 2.628 0.985 2.85 00 192.86504/27/2010,10:01:350 28.7960.888 2.836 0.985 2.85 00 192.88404/27/2010,10:02:350 28.7970.888 2.692 0.985 2.853 00 192.99404/27/2010,10:03:350 28.7990.888 2.56 0.985 2.849 00 193.12604/27/2010,10:04:350 28.7990.888 2.493 0.985 2.85 00 193.03604/27/2010,10:05:350 28.80.888 2.911 0.985 2.853 00 193.16604/27/2010,10:06:350 28.7980.888 2.757 0.985 2.854 00 193.45604/27/2010,10:07:350 28.7970.888 2.712 0.985 2.854 00 193.32404/27/2010,10:08:350 28.7960.888 2.642 0.985 2.852 00 193.30204/27/2010,10:09:350 28.7950.888 2.78 0.985 2.857 00 193.18804/27/2010,10:10:350 28.7940.888 2.852 0.985 2.854 00 193.19204/27/2010,10:11:350 28.7930.888 2.83 0.985 2.853 00 193.09204/27/2010,10:12:350 28.7950.888 2.799 0.985 2.85 00 193.02104/27/2010,10:13:350 28.7940.888 2.574 0.985 2.854 00 193.20104/27/2010,10:14:350 28.7960.888 2.856 0.985 2.852 00 193.0404/27/2010,10:15:350 28.7950.888 2.741 0.985 2.851 00 192.43904/27/2010,10:16:350 28.7940.888 2.808 0.985 2.849 00 192.26504/27/2010,10:17:360 28.7930.888 2.789 0.985 2.852 00 191.68404/27/2010,10:18:360 28.7950.888 2.772 0.985 2.851 00 191.21904/27/2010,10:19:360 28.7940.888 2.623 0.985 2.853 00 190.88904/27/2010,10:20:360 28.7960.888 2.746 0.985 2.853 00 190.31704/27/2010,10:21:360 28.7950.888 2.731 0.985 2.853 00 189.80804/27/2010,10:22:370 28.7960.888 2.813 0.985 2.85 00 189.37204/27/2010,10:23:370 28.7940.888 2.911 0.985 2.85 00 188.92204/27/2010,10:24:370 28.7940.888 2.773 0.985 2.852 00 188.5804/27/2010,10:25:370 28.7940.888 2.78 0.985 2.848 00 188.02904/27/2010,10:26:370 28.7930.888 2.634 0.985 2.977 00 187.66104/27/2010,10:27:370 28.7930.888 2.818 0.985 3.017 00 187.37704/27/2010,10:28:370 28.7930.888 2.856 0.985 3.019 00 187.0904/27/2010,10:29:370 28.7930.888 2.902 0.985 3.019 00 186.85204/27/2010,10:30:370 28.7930.888 2.813 0.985 3.015 00 186.73204/27/2010,10:31:370 28.7930.888 2.791 0.985 3.02 00 186.84Time:date,hh:mm:ss04/27/2010,09:57:3504/27/2010,09:58:3504/27/2010,09:59:3504/27/2010,10:00:3504/27/2010,10:01:3504/27/2010,10:02:3504/27/2010,10:03:3504/27/2010,10:04:3504/27/2010,10:05:3504/27/2010,10:06:3504/27/2010,10:07:3504/27/2010,10:08:3504/27/2010,10:09:3504/27/2010,10:10:3504/27/2010,10:11:3504/27/2010,10:12:3504/27/2010,10:13:3504/27/2010,10:14:3504/27/2010,10:15:3504/27/2010,10:16:3504/27/2010,10:17:3604/27/2010,10:18:3604/27/2010,10:19:3604/27/2010,10:20:3604/27/2010,10:21:3604/27/2010,10:22:3704/27/2010,10:23:3704/27/2010,10:24:3704/27/2010,10:25:3704/27/2010,10:26:3704/27/2010,10:27:3704/27/2010,10:28:3704/27/2010,10:29:3704/27/2010,10:30:3704/27/2010,10:31:37Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.348 250.49568.517 68.042500 70.108 73.887274.353 250.80368.512 68.066500 70.114 73.891274.436 251.79268.457 68.056500 70.117 73.839274.35 249.66568.47 68.086500 70.146 73.946274.367 251.82668.44 68.084500 70.125 73.89274.593 250.78668.483 68.098500 70.164 73.913274.354 250.4268.48 68.097500 70.153 73.941274.4 252.16468.486 68.106500 70.166 73.934274.618 250.20668.512 68.101500 70.169 73.986274.442 251.49668.63 68.133500 70.211 74.011274.399 251.8568.706 68.111500 70.175 74.04274.538 250.21268.757 68.138500 70.24 74.148274.488 252.1868.759 68.145500 70.236 74.154274.378 250.9268.783 68.167500 70.264 74.198274.46 250.65568.809 68.157500 70.285 74.088274.452 252.45168.838 68.185500 70.313 74.055274.301 249.81768.881 68.21500 70.339 74.12274.215 251.4768.959 68.221500 70.345 74.053274.396 251.65168.978 68.255500 70.377 74.031274.352 249.69868.874 68.236500 70.374 74.042274.092 251.90768.829 68.28500 70.41 74.061274.235 250.26868.787 68.266500 70.403 74.057274.273 250.89768.859 68.362500 70.444 74.103274.178 251.93368.951 68.37500 70.451 74.149274.232 249.83169.058 68.402500 70.486 74.177274.081 251.71469.108 68.404500 70.507 74.176274.146 251.20169.137 68.419500 70.532 74.222274.3 250.09969.201 68.449500 70.605 74.239274.02 252.11569.165 68.441500 70.584 74.203274.085 250.28169.228 68.493500 70.645 74.227274.228 251.12669.286 68.495500 70.648 74.213274.11 252.14169.389 68.529500 70.686 74.284274.056 249.60969.435 68.558500 70.714 74.329274.019 251.87769.495 68.611500 70.745 74.33274.068 251.35769.557 68.696500 70.787 74.311Time:date,hh:mm:ss04/27/2010,09:57:3504/27/2010,09:58:3504/27/2010,09:59:3504/27/2010,10:00:3504/27/2010,10:01:3504/27/2010,10:02:3504/27/2010,10:03:3504/27/2010,10:04:3504/27/2010,10:05:3504/27/2010,10:06:3504/27/2010,10:07:3504/27/2010,10:08:3504/27/2010,10:09:3504/27/2010,10:10:3504/27/2010,10:11:3504/27/2010,10:12:3504/27/2010,10:13:3504/27/2010,10:14:3504/27/2010,10:15:3504/27/2010,10:16:3504/27/2010,10:17:3604/27/2010,10:18:3604/27/2010,10:19:3604/27/2010,10:20:3604/27/2010,10:21:3604/27/2010,10:22:3704/27/2010,10:23:3704/27/2010,10:24:3704/27/2010,10:25:3704/27/2010,10:26:3704/27/2010,10:27:3704/27/2010,10:28:3704/27/2010,10:29:3704/27/2010,10:30:3704/27/2010,10:31:37Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal75.636 188.411 177.146 195.268 188.07875.675 191.672 180.2 198.652 191.32575.712 194.939 183.271 202.043 194.5975.749 198.198 186.381 205.425 197.89775.784 201.459 189.437 208.81 201.14675.821 204.741 192.51 212.215 204.41375.854 208.009 195.578 215.607 207.67575.89 211.269 198.662 218.99 210.95475.923 214.536 201.774 222.38 214.26375.957 217.79 204.824 225.757 217.50675.987 221.064 207.879 229.155 220.75476.019 224.357 210.964 232.574 224.03576.053 227.622 214.065 235.962 227.33376.085 230.889 217.123 239.355 230.58576.118 234.159 220.199 242.749 233.85676.147 237.423 223.258 246.137 237.1176.178 240.689 226.335 249.527 240.38376.208 243.956 229.446 252.919 243.69276.241 247.22 232.491 256.308 246.93176.273 250.489 235.547 259.702 250.18276.302 253.798 238.673 263.138 253.50876.334 257.073 241.755 266.538 256.78776.362 260.355 244.855 269.947 260.08476.392 263.637 247.921 273.354 263.34676.423 266.912 250.972 276.756 266.59376.45 270.192 254.043 280.161 269.8676.481 273.467 257.15 283.563 273.16576.51 276.737 260.204 286.959 276.41676.537 280.01 263.274 290.359 279.68376.57 283.166 266.197 293.637 282.79576.598 286.285 269.09 296.877 285.87476.627 289.397 271.967 300.11 288.93676.657 292.572 274.835 303.409 291.98976.685 295.671 277.74 306.628 295.08176.713 298.796 280.585 309.876 298.111Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,10:32:370 28.7940.888 2.958 0.985 3.022 00 186.6404/27/2010,10:33:370 28.7940.888 3.011 0.985 3.02 00 186.37104/27/2010,10:34:370 28.7940.888 2.886 0.985 3.025 00 186.06504/27/2010,10:35:370 28.7930.888 2.937 0.985 3.027 00 185.82104/27/2010,10:36:370 28.7910.888 2.752 0.985 3.022 00 185.60104/27/2010,10:37:370 28.7910.888 2.794 0.985 3.022 00 185.41504/27/2010,10:38:370 28.7910.888 2.895 0.985 3.027 00 185.26204/27/2010,10:39:370 28.790.888 3.014 0.985 3.022 00 185.10904/27/2010,10:40:370 28.7910.888 2.952 0.985 3.023 00 185.00904/27/2010,10:41:370 28.7930.888 3.143 0.985 3.026 00 184.79604/27/2010,10:42:370 28.7930.888 2.835 0.985 3.023 00 184.67904/27/2010,10:43:370 28.7920.888 2.854 0.985 3.026 00 184.55104/27/2010,10:44:370 28.7910.888 2.745 0.985 3.023 00 184.54804/27/2010,10:45:370 28.790.888 2.707 0.985 3.023 00 184.53204/27/2010,10:46:380 28.7870.888 2.859 0.985 3.021 00 184.35404/27/2010,10:47:380 28.7890.888 2.975 0.985 3.02 00 184.34504/27/2010,10:48:380 28.7880.888 2.916 0.985 3.023 00 184.55504/27/2010,10:49:380 28.7890.888 2.716 0.985 3.021 00 184.35504/27/2010,10:50:380 28.790.888 3.063 0.985 3.025 00 184.35904/27/2010,10:51:380 28.7910.888 3.002 0.985 3.024 00 184.31304/27/2010,10:52:380 28.7910.888 2.852 0.985 3.024 00 184.23304/27/2010,10:53:380 28.7920.888 2.88 0.985 3.024 00 184.13404/27/2010,10:54:380 28.7920.888 2.959 0.985 3.024 00 184.02204/27/2010,10:55:380 28.7950.888 2.829 0.985 3.029 00 184.01904/27/2010,10:56:380 28.7940.888 3.024 0.984 3.026 00 183.92304/27/2010,10:57:380 28.7940.888 3.1 0.984 3.023 00 183.72404/27/2010,10:58:380 28.7950.888 2.899 0.984 3.024 00 183.83404/27/2010,10:59:380 28.7940.888 2.808 0.984 3.022 00 183.8204/27/2010,11:00:380 28.7950.888 2.73 0.984 3.022 00 183.5704/27/2010,11:01:380 28.7950.888 2.887 0.984 3.024 00 183.36904/27/2010,11:02:380 28.7950.888 3.042 0.984 3.022 00 183.23504/27/2010,11:03:380 28.7960.888 2.788 0.984 3.025 00 183.01804/27/2010,11:04:380 28.7960.888 2.796 0.984 3.023 00 182.82304/27/2010,11:05:380 28.7970.888 2.869 0.984 3.021 00 182.82804/27/2010,11:06:380 28.7970.888 2.836 0.984 3.021 00 182.755Time:date,hh:mm:ss04/27/2010,10:32:3704/27/2010,10:33:3704/27/2010,10:34:3704/27/2010,10:35:3704/27/2010,10:36:3704/27/2010,10:37:3704/27/2010,10:38:3704/27/2010,10:39:3704/27/2010,10:40:3704/27/2010,10:41:3704/27/2010,10:42:3704/27/2010,10:43:3704/27/2010,10:44:3704/27/2010,10:45:3704/27/2010,10:46:3804/27/2010,10:47:3804/27/2010,10:48:3804/27/2010,10:49:3804/27/2010,10:50:3804/27/2010,10:51:3804/27/2010,10:52:3804/27/2010,10:53:3804/27/2010,10:54:3804/27/2010,10:55:3804/27/2010,10:56:3804/27/2010,10:57:3804/27/2010,10:58:3804/27/2010,10:59:3804/27/2010,11:00:3804/27/2010,11:01:3804/27/2010,11:02:3804/27/2010,11:03:3804/27/2010,11:04:3804/27/2010,11:05:3804/27/2010,11:06:38Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.049 250.17769.655 68.711500 70.793 74.328274.032 252.3969.764 68.77500 70.854 74.348274.012 250.52369.811 68.774500 70.919 74.377274.013 251.07669.933 68.833500 70.985 74.624274.045 252.47970.069 68.882500 71.015 74.724273.98 249.98470.116 68.935500 71.073 74.835274.064 251.89570.173 69.042500 71.125 74.882274.007 251.18670.32 69.064500 71.154 74.942274.03 250.05370.43 69.14500 71.267 75.115274.06 252.69270.488 69.17500 71.303 75.179274.004 249.25370.646 69.245500 71.38 75.328273.815 251.49270.62 69.318500 71.404 75.362273.969 251.17570.679 69.39500 71.526 75.369274.052 249.31870.647 69.427500 71.553 75.343273.843 251.80470.541 69.499500 71.622 75.23273.852 249.66170.371 69.513500 71.639 75.163274.01 251.10270.441 69.619500 71.684 75.158274.009 251.72170.502 69.659500 71.697 75.217274.011 249.64370.653 69.722500 71.76 75.232273.998 252.28770.68 69.728500 71.787 75.349274.148 250.81470.729 69.785500 71.888 75.499274.052 250.42270.846 69.844500 71.925 75.588274.03 252.41570.932 69.94500 71.961 75.708274.11 249.47670.995 69.974500 71.991 75.721274.023 251.81671.025 70.008500 72.02 75.752274.073 251.42471.105 70.052500 72.058 75.861273.995 249.58271.181 70.11500 72.101 75.967274.002 252.35771.265 70.152500 72.184 76.071274.2 250.42771.293 70.18500 72.223 76.094271.037 250.93371.356 70.283500 72.278 76.164272.188 252.31471.377 70.324500 72.294 76.157193.765 250.14871.367 70.391500 72.354 76.319133.663 251.99971.177 70.407500 72.366 76.223190.681 251.63271.124 70.451500 72.41 76.173202.214 249.97571.143 70.472500 72.427 76.176Time:date,hh:mm:ss04/27/2010,10:32:3704/27/2010,10:33:3704/27/2010,10:34:3704/27/2010,10:35:3704/27/2010,10:36:3704/27/2010,10:37:3704/27/2010,10:38:3704/27/2010,10:39:3704/27/2010,10:40:3704/27/2010,10:41:3704/27/2010,10:42:3704/27/2010,10:43:3704/27/2010,10:44:3704/27/2010,10:45:3704/27/2010,10:46:3804/27/2010,10:47:3804/27/2010,10:48:3804/27/2010,10:49:3804/27/2010,10:50:3804/27/2010,10:51:3804/27/2010,10:52:3804/27/2010,10:53:3804/27/2010,10:54:3804/27/2010,10:55:3804/27/2010,10:56:3804/27/2010,10:57:3804/27/2010,10:58:3804/27/2010,10:59:3804/27/2010,11:00:3804/27/2010,11:01:3804/27/2010,11:02:3804/27/2010,11:03:3804/27/2010,11:04:3804/27/2010,11:05:3804/27/2010,11:06:38Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal76.743 301.903 283.503 313.104 301.21776.77 305.07 286.339 316.396 304.23776.798 308.173 289.261 319.621 307.34976.83 311.276 292.083 322.846 310.35476.86 314.378 294.992 326.071 313.45276.889 317.551 297.832 329.37 316.47876.922 320.648 300.715 332.591 319.5576.953 323.755 303.577 335.822 322.59876.981 326.868 306.459 339.06 325.6777.015 330.045 309.315 342.365 328.71377.047 333.138 312.193 345.582 331.78177.08 336.243 315.053 348.813 334.8377.115 339.363 317.961 352.058 337.9377.148 342.534 320.804 355.359 340.96277.183 345.634 323.695 358.586 344.04577.22 348.74 326.562 361.819 347.10377.253 351.85 329.422 365.057 350.15477.288 355.024 332.318 368.362 353.24377.325 358.123 335.144 371.589 356.25777.356 361.225 338.065 374.819 359.37277.391 364.328 340.901 378.05 362.39877.427 367.492 343.794 381.345 365.48577.461 370.586 346.625 384.568 368.50677.5 373.688 349.511 387.799 371.58577.537 376.802 352.359 391.043 374.62477.57 379.961 355.242 394.334 377.70177.608 383.056 358.096 397.559 380.74677.646 386.17 360.973 400.803 383.81877.68 389.283 363.833 404.047 386.87177.718 392.441 366.71 407.339 389.94277.757 395.544 369.568 410.573 392.99377.793 398.653 372.468 413.813 396.08977.832 401.761 375.313 417.053 399.12777.871 404.94 378.2 420.367 402.2177.906 408.05 381.063 423.61 405.266Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,11:07:380 28.7960.888 2.824 0.984 3.021 00 182.60704/27/2010,11:08:380 28.7970.888 2.861 0.984 3.021 00 182.65404/27/2010,11:09:380 28.7970.888 2.891 0.984 3.025 00 182.62804/27/2010,11:10:390 28.7970.888 2.998 0.984 3.025 00 182.40404/27/2010,11:11:390 28.7990.888 3.249 0.984 3.027 00 182.33204/27/2010,11:12:390 28.7990.888 2.865 0.984 3.03 00 182.23304/27/2010,11:13:390 28.80.888 2.782 0.984 3.031 00 181.99404/27/2010,11:14:390 28.80.888 2.909 0.984 3.03 00 181.83404/27/2010,11:15:390 28.8010.888 2.732 0.984 3.032 00 181.67804/27/2010,11:16:390 28.8010.888 2.895 0.984 3.036 00 181.72704/27/2010,11:17:390 28.80.888 3.081 0.984 3.032 00 181.74804/27/2010,11:18:390 28.8010.888 2.703 0.984 3.03 00 181.20304/27/2010,11:19:390 28.8010.888 2.804 0.984 3.033 00 181.30204/27/2010,11:20:390 28.8010.888 2.88 0.984 3.033 00 181.32204/27/2010,11:21:390 28.8020.888 2.826 0.984 3.031 00 181.23604/27/2010,11:22:390 28.8020.888 2.801 0.984 3.035 00 181.17104/27/2010,11:23:390 28.8050.888 2.852 0.984 3.033 00 181.03304/27/2010,11:24:390 28.8050.888 2.936 0.984 3.031 00 180.94104/27/2010,11:25:390 28.8050.888 2.822 0.984 3.034 00 180.8604/27/2010,11:26:390 28.8060.888 2.771 0.984 3.034 00 180.75304/27/2010,11:27:390 28.8080.888 2.733 0.984 3.034 00 180.83504/27/2010,11:28:390 28.8060.888 2.942 0.984 3.033 00 180.72204/27/2010,11:29:390 28.8080.888 2.858 0.984 3.033 00 180.54704/27/2010,11:30:390 28.8070.888 2.952 0.984 3.034 00 180.50404/27/2010,11:31:390 28.8080.888 2.865 0.984 3.032 00 180.51304/27/2010,11:32:390 28.8060.888 2.791 0.984 3.03 00 180.37404/27/2010,11:33:390 28.8040.888 2.847 0.984 3.03 00 180.26304/27/2010,11:34:390 28.8060.888 2.899 0.984 3.031 00 180.19904/27/2010,11:35:400 28.8040.888 3.257 0.984 3.03 00 180.11204/27/2010,11:36:400 28.8040.888 2.612 0.984 3.029 00 179.99104/27/2010,11:37:400 28.8020.888 2.911 0.984 3.027 00 179.93704/27/2010,11:38:400 28.8040.888 2.766 0.984 3.031 00 179.7904/27/2010,11:39:400 28.8040.888 2.897 0.984 3.027 00 179.56804/27/2010,11:40:400 28.8050.888 2.946 0.984 3.03 00 179.47704/27/2010,11:41:400 28.8040.888 2.933 0.984 3.033 00 179.448Time:date,hh:mm:ss04/27/2010,11:07:3804/27/2010,11:08:3804/27/2010,11:09:3804/27/2010,11:10:3904/27/2010,11:11:3904/27/2010,11:12:3904/27/2010,11:13:3904/27/2010,11:14:3904/27/2010,11:15:3904/27/2010,11:16:3904/27/2010,11:17:3904/27/2010,11:18:3904/27/2010,11:19:3904/27/2010,11:20:3904/27/2010,11:21:3904/27/2010,11:22:3904/27/2010,11:23:3904/27/2010,11:24:3904/27/2010,11:25:3904/27/2010,11:26:3904/27/2010,11:27:3904/27/2010,11:28:3904/27/2010,11:29:3904/27/2010,11:30:3904/27/2010,11:31:3904/27/2010,11:32:3904/27/2010,11:33:3904/27/2010,11:34:3904/27/2010,11:35:4004/27/2010,11:36:4004/27/2010,11:37:4004/27/2010,11:38:4004/27/2010,11:39:4004/27/2010,11:40:4004/27/2010,11:41:40Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF144.765 252.81171.184 70.507500 72.452 76.189145.542 249.24971.26 70.586500 72.498 76.234125.196 251.89471.215 70.619500 72.525 76.211105.569 250.57971.292 70.649500 72.544 76.23586.712 249.89271.291 70.661500 72.538 76.2483.667 252.44971.312 70.692500 72.575 76.22981.69 249.30671.297 70.684500 72.581 76.20181.27 252.43771.342 70.733500 72.613 76.17485.142 250.71471.257 70.736500 72.586 76.08493.469 250.6871.305 70.783500 72.635 76.16588.533 251.85371.217 70.78500 72.632 76.14288.191 249.4171.296 70.816500 72.651 76.11592.666 252.21671.312 70.814500 72.653 76.19100.326 249.671.352 70.844500 72.689 76.28890.546 250.85771.323 70.878500 72.672 76.35981.803 250.72971.203 70.944500 72.694 76.33876.546 249.59371.091 70.911500 72.691 76.29781.922 252.10171.109 70.956500 72.697 76.33997.148 249.03871.101 70.968500 72.698 76.249126.294 251.70371.071 70.976500 72.694 76.259150.975 250.20871.024 70.958500 72.664 76.26148.856 250.11670.924 70.998500 72.69 76.288137.228 251.18770.837 70.958500 72.642 76.208153.283 249.52370.85 70.989500 72.667 76.209142.996 252.17270.782 70.963500 72.64 76.212113.364 249.60670.755 70.977500 72.63 76.192110.604 251.45570.762 70.965500 72.637 76.172121.525 250.67370.735 70.945500 72.599 76.172133.892 250.48670.741 70.965500 72.617 76.222157.77 252.3170.732 70.949500 72.583 76.178167.564 249.32670.693 70.912500 72.577 76.115167.326 252.10170.695 70.947500 72.578 76.079159.052 251.00370.536 70.87500 72.547 76.033233.569 250.94870.625 70.857500 72.538 76.089210.316 252.7670.678 70.869500 72.563 76.122Time:date,hh:mm:ss04/27/2010,11:07:3804/27/2010,11:08:3804/27/2010,11:09:3804/27/2010,11:10:3904/27/2010,11:11:3904/27/2010,11:12:3904/27/2010,11:13:3904/27/2010,11:14:3904/27/2010,11:15:3904/27/2010,11:16:3904/27/2010,11:17:3904/27/2010,11:18:3904/27/2010,11:19:3904/27/2010,11:20:3904/27/2010,11:21:3904/27/2010,11:22:3904/27/2010,11:23:3904/27/2010,11:24:3904/27/2010,11:25:3904/27/2010,11:26:3904/27/2010,11:27:3904/27/2010,11:28:3904/27/2010,11:29:3904/27/2010,11:30:3904/27/2010,11:31:3904/27/2010,11:32:3904/27/2010,11:33:3904/27/2010,11:34:3904/27/2010,11:35:4004/27/2010,11:36:4004/27/2010,11:37:4004/27/2010,11:38:4004/27/2010,11:39:4004/27/2010,11:40:4004/27/2010,11:41:40Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal77.944 411.154 383.928 426.846 408.32677.981 414.265 386.81 430.09 411.40478.017 417.438 389.65 433.398 414.43778.052 420.527 392.557 436.62 417.54178.09 423.638 395.385 439.863 420.56278.127 426.746 398.282 443.106 423.65678.163 429.901 401.105 446.395 426.67178.199 432.997 403.99 449.624 429.75278.235 436.104 406.83 452.864 432.78578.272 439.208 409.697 456.102 435.84878.305 442.366 412.545 459.396 438.88978.34 445.454 415.41 462.617 441.94978.376 448.561 418.263 465.857 444.99678.413 451.658 421.153 469.087 448.08378.447 454.824 423.993 472.39 451.11678.48 457.912 426.844 475.611 454.16178.514 461.025 429.732 478.859 457.24678.549 464.124 432.546 482.092 460.25178.582 467.281 435.464 485.385 463.36978.608 470.371 438.276 488.608 466.37278.64 473.485 441.164 491.856 469.45578.672 476.585 443.995 495.09 472.47978.703 479.746 446.872 498.388 475.55178.733 482.836 449.72 501.611 478.59278.762 485.946 452.582 504.855 481.64878.788 489.045 455.442 508.087 484.70378.817 492.211 458.331 511.39 487.78878.844 495.308 461.167 514.621 490.81678.871 498.41 464.043 517.857 493.88778.896 501.521 466.909 521.103 496.94778.922 504.684 469.757 524.402 499.98978.945 507.786 472.655 527.638 503.08378.967 510.884 475.478 530.869 506.09878.989 514.01 478.399 534.13 509.21779.011 517.157 481.21 537.412 512.218Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,11:42:400 28.8020.888 2.773 0.984 3.029 00 179.58504/27/2010,11:43:400 28.8020.888 2.696 0.984 3.03 00 179.71104/27/2010,11:44:400 28.8020.888 2.861 0.984 3.031 00 179.76604/27/2010,11:45:400 28.8040.888 2.86 0.984 3.032 00 179.74404/27/2010,11:46:400 28.8030.888 2.938 0.984 3.034 00 179.67804/27/2010,11:47:400 28.8020.888 2.953 0.984 3.033 00 179.68404/27/2010,11:48:400 28.80.888 2.925 0.984 3.029 00 179.68704/27/2010,11:49:400 28.7990.888 2.844 0.984 3.03 00 179.63604/27/2010,11:50:400 28.7990.888 2.703 0.984 3.029 00 179.6104/27/2010,11:51:400 28.7990.888 3.055 0.984 3.025 00 179.71304/27/2010,11:52:400 28.80.888 2.717 0.984 3.024 00 179.75304/27/2010,11:53:400 28.7990.888 2.865 0.984 3.025 00 179.41704/27/2010,11:54:400 28.80.888 2.902 0.984 3.017 00 179.7504/27/2010,11:55:400 28.8020.888 2.938 0.984 3.02 00 181.24704/27/2010,11:56:400 28.8030.888 2.753 0.984 3.022 00 182.21604/27/2010,11:57:400 28.8020.888 2.801 0.984 3.026 00 183.15804/27/2010,11:58:400 28.8020.888 2.84 0.984 3.029 00 183.79804/27/2010,11:59:410 28.8020.888 2.885 0.984 3.028 00 184.32604/27/2010,12:00:410 28.8020.888 2.881 0.984 3.026 00 184.56404/27/2010,12:01:410 28.8010.888 2.732 0.984 3.028 00 185.06904/27/2010,12:02:410 28.80.888 2.937 0.984 3.03 00 185.44504/27/2010,12:03:410 28.8010.888 2.906 0.984 3.032 00 185.6804/27/2010,12:04:410 28.8010.888 2.85 0.984 3.033 00 185.95704/27/2010,12:05:410 28.80.888 2.795 0.984 3.034 00 186.13704/27/2010,12:06:410 28.80.888 3.052 0.984 3.035 00 186.33804/27/2010,12:07:410 28.80.888 2.934 0.984 3.038 00 186.42204/27/2010,12:08:410 28.7990.888 2.647 0.984 3.036 00 186.59304/27/2010,12:09:410 28.7990.888 2.963 0.984 3.041 00 186.69104/27/2010,12:10:410 28.80.888 2.895 0.984 3.042 00 186.62304/27/2010,12:11:410 28.80.888 2.774 0.984 3.038 00 186.92704/27/2010,12:12:410 28.8010.888 2.857 0.984 3.041 00 187.20404/27/2010,12:13:410 28.8010.888 2.862 0.984 3.043 00 187.21904/27/2010,12:14:410 28.8010.888 2.951 0.984 3.043 00 187.22104/27/2010,12:15:410 28.8010.888 2.906 0.984 3.044 00 187.24804/27/2010,12:16:410 28.8020.888 2.861 0.984 3.043 00 187.318Time:date,hh:mm:ss04/27/2010,11:42:4004/27/2010,11:43:4004/27/2010,11:44:4004/27/2010,11:45:4004/27/2010,11:46:4004/27/2010,11:47:4004/27/2010,11:48:4004/27/2010,11:49:4004/27/2010,11:50:4004/27/2010,11:51:4004/27/2010,11:52:4004/27/2010,11:53:4004/27/2010,11:54:4004/27/2010,11:55:4004/27/2010,11:56:4004/27/2010,11:57:4004/27/2010,11:58:4004/27/2010,11:59:4104/27/2010,12:00:4104/27/2010,12:01:4104/27/2010,12:02:4104/27/2010,12:03:4104/27/2010,12:04:4104/27/2010,12:05:4104/27/2010,12:06:4104/27/2010,12:07:4104/27/2010,12:08:4104/27/2010,12:09:4104/27/2010,12:10:4104/27/2010,12:11:4104/27/2010,12:12:4104/27/2010,12:13:4104/27/2010,12:14:4104/27/2010,12:15:4104/27/2010,12:16:41Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF181.022 249.70770.619 70.838500 72.527 76.072200.72 252.16770.616 70.818500 72.511 76.085236.917 251.04470.671 70.848500 72.539 76.134249.322 250.64270.727 70.836500 72.525 76.207254.702 252.89570.728 70.796500 72.504 76.256271.934 249.9970.737 70.819500 72.502 76.282263.788 252.16570.697 70.838500 72.529 76.231264.097 250.97470.574 70.816500 72.519 76.199258.652 250.27570.494 70.791500 72.473 76.202240.924 252.43570.483 70.794500 72.434 76.175246.617 249.56370.639 70.827500 72.525 76.238241.451 252.33370.618 70.797500 72.484 76.216216.488 250.37670.594 70.788500 72.415 76.239223.424 250.80270.499 70.78500 72.408 76.212212.704 252.22670.466 70.774500 72.411 76.184209.183 249.89970.435 70.789500 72.417 76.154193.802 252.38370.442 70.784500 72.403 76.193210.92 250.53670.408 70.758500 72.372 76.139226.09 250.69270.407 70.733500 72.356 76.134198.007 252.2870.426 70.735500 72.337 76.155192.877 250.0470.551 70.768500 72.358 76.169188.43 252.24570.559 70.739500 72.356 76.146177.108 251.49570.596 70.732500 72.352 76.22194.357 250.52570.666 70.729500 72.337 76.241219.059 253.0370.648 70.727500 72.322 76.186226.497 249.40370.479 70.712500 72.309 76.128234.078 252.48570.48 70.691500 72.302 76.123228.072 250.07870.442 70.68150072.3 76.117213.594 251.11470.382 70.704500 72.324 76.126205.607 252.08670.427 70.732500 72.341 76.145211.98 249.68570.412 70.732500 72.318 76.157222.553 252.55270.444 70.728500 72.302 76.152223.128 250.54970.435 70.71550072.3 76.164235.041 250.90670.423 70.701500 72.296 76.142239.181 251.94970.446 70.68500 72.286 76.128Time:date,hh:mm:ss04/27/2010,11:42:4004/27/2010,11:43:4004/27/2010,11:44:4004/27/2010,11:45:4004/27/2010,11:46:4004/27/2010,11:47:4004/27/2010,11:48:4004/27/2010,11:49:4004/27/2010,11:50:4004/27/2010,11:51:4004/27/2010,11:52:4004/27/2010,11:53:4004/27/2010,11:54:4004/27/2010,11:55:4004/27/2010,11:56:4004/27/2010,11:57:4004/27/2010,11:58:4004/27/2010,11:59:4104/27/2010,12:00:4104/27/2010,12:01:4104/27/2010,12:02:4104/27/2010,12:03:4104/27/2010,12:04:4104/27/2010,12:05:4104/27/2010,12:06:4104/27/2010,12:07:4104/27/2010,12:08:4104/27/2010,12:09:4104/27/2010,12:10:4104/27/2010,12:11:4104/27/2010,12:12:4104/27/2010,12:13:4104/27/2010,12:14:4104/27/2010,12:15:4104/27/2010,12:16:41Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal79.032 520.276 484.117 540.665 515.32279.053 523.372 486.942 543.894 518.33979.073 526.491 489.824 547.147 521.41679.092 529.632 492.674 550.424 524.45979.11 532.759 495.544 553.685 527.52379.129 535.842 498.394 556.9 530.56679.146 538.959 501.274 560.152 533.64279.16 542.096 504.12 563.424 536.68179.176 545.233 507.016 566.697 539.77379.192 548.347 509.864 569.944 542.81579.208 551.473 512.748 573.205 545.89479.221 554.587 515.617 576.453 548.95879.236 557.774 518.485 579.777 552.0279.252 560.882 521.377 583.019 555.10779.265 564.002 524.229 586.272 558.15279.279 567.116 527.133 589.52 561.25279.292 570.285 529.953 592.825 564.26379.304 573.399 532.88 596.073 567.38879.316 576.499 535.713 599.305 570.41279.327 579.629 538.609 602.57 573.50279.337 582.765 541.436 605.841 576.52179.348 585.897 544.323 609.107 579.60279.355 588.995 547.164 612.338 582.63579.367 592.102 550.04 615.578 585.70579.375 595.229 552.885 618.839 588.74379.382 598.354 555.752 622.098 591.80379.387 601.435 558.598 625.312 594.8479.392 604.539 561.473 628.548 597.9179.4 607.679 564.326 631.823 600.95579.405 610.782 567.154 635.059 603.97379.409 613.86 570.06 638.269 607.07579.415 616.967 572.866 641.509 610.07179.421 620.119 575.742 644.796 613.14179.424 623.201 578.568 648.01 616.15779.428 626.301 581.432 651.243 619.214Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,12:17:410 28.8020.888 2.912 0.984 3.043 00 187.29704/27/2010,12:18:410 28.8020.888 2.925 0.984 3.044 00 187.49204/27/2010,12:19:410 28.8010.888 2.834 0.984 3.045 00 187.5904/27/2010,12:20:410 28.8020.888 2.856 0.984 3.044 00 187.94504/27/2010,12:21:410 28.8020.888 2.868 0.984 3.042 00 187.46704/27/2010,12:22:410 28.8030.8883 0.984 3.046 00 187.44704/27/2010,12:23:420 28.8030.888 2.942 0.984 3.043 00 187.604/27/2010,12:24:420 28.8030.888 2.748 0.984 3.045 00 187.77904/27/2010,12:25:420 28.8040.888 2.856 0.984 3.046 00 187.71204/27/2010,12:26:420 28.8040.888 2.817 0.984 3.044 00 187.48904/27/2010,12:27:420 28.8050.888 2.751 0.984 3.045 00 187.6504/27/2010,12:28:420 28.8060.888 2.874 0.984 3.043 00 187.66504/27/2010,12:29:420 28.8040.888 2.869 0.984 3.046 00 187.64504/27/2010,12:30:420 28.8030.888 2.775 0.984 3.046 00 187.604/27/2010,12:31:420 28.8020.888 2.99 0.984 3.041 00 187.50904/27/2010,12:32:420 28.8010.888 2.68 0.984 3.04 00 187.44104/27/2010,12:33:420 28.80.888 2.859 0.984 3.036 00 187.47804/27/2010,12:34:420 28.80.888 3.166 0.984 3.037 00 187.43704/27/2010,12:35:420 28.80.888 2.899 0.984 3.03 00 187.52204/27/2010,12:36:420 28.80.888 2.769 0.984 3.029 00 187.54204/27/2010,12:37:420 28.80.888 2.894 0.984 3.03 00 187.57204/27/2010,12:38:420 28.8010.888 2.769 0.984 3.027 00 187.56104/27/2010,12:39:420 28.8010.888 2.668 0.984 3.032 00 187.48604/27/2010,12:40:420 28.8010.888 2.955 0.984 3.029 00 187.41304/27/2010,12:41:420 28.8010.888 2.921 0.984 3.032 00 187.35904/27/2010,12:42:420 28.8010.888 2.978 0.984 3.031 00 187.24904/27/2010,12:43:420 28.80.888 2.919 0.984 3.033 00 187.26204/27/2010,12:44:420 28.7980.888 2.99 0.984 3.033 00 187.1904/27/2010,12:45:420 28.7970.888 3.062 0.984 3.034 00 187.17704/27/2010,12:46:420 28.7970.888 2.865 0.984 3.032 00 187.09804/27/2010,12:47:430 28.7970.888 2.882 0.984 3.032 00 186.99704/27/2010,12:48:430 28.7960.888 3.098 0.984 3.033 00 186.84904/27/2010,12:49:430 28.7940.888 2.947 0.984 3.034 00 186.72604/27/2010,12:50:430 28.7930.888 2.886 0.984 3.035 00 186.72704/27/2010,12:51:430 28.7910.888 2.924 0.984 3.033 00 186.647Time:date,hh:mm:ss04/27/2010,12:17:4104/27/2010,12:18:4104/27/2010,12:19:4104/27/2010,12:20:4104/27/2010,12:21:4104/27/2010,12:22:4104/27/2010,12:23:4204/27/2010,12:24:4204/27/2010,12:25:4204/27/2010,12:26:4204/27/2010,12:27:4204/27/2010,12:28:4204/27/2010,12:29:4204/27/2010,12:30:4204/27/2010,12:31:4204/27/2010,12:32:4204/27/2010,12:33:4204/27/2010,12:34:4204/27/2010,12:35:4204/27/2010,12:36:4204/27/2010,12:37:4204/27/2010,12:38:4204/27/2010,12:39:4204/27/2010,12:40:4204/27/2010,12:41:4204/27/2010,12:42:4204/27/2010,12:43:4204/27/2010,12:44:4204/27/2010,12:45:4204/27/2010,12:46:4204/27/2010,12:47:4304/27/2010,12:48:4304/27/2010,12:49:4304/27/2010,12:50:4304/27/2010,12:51:43Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF231.491 249.44570.401 70.678500 72.257 75.993216.014 252.59270.312 70.675500 72.248 75.931210.92 250.37270.337 70.675500 72.242 75.973225.512 251.18870.333 70.669500 72.237 75.959244.935 251.56570.3 70.659500 72.223 75.874249.13 249.70470.172 70.639500 72.195 75.789259.897 252.61870.174 70.625500 72.188 75.843254.033 249.76270.065 70.621500 72.178 75.843252.172 251.87270.061 70.619500 72.134 75.861254.718 251.25770.11 70.61500 72.083 75.87280.725 250.35970.088 70.575500 72.076 75.815262.595 252.88870.079 70.529500 72.071 75.807262.49 249.44570.053 70.51500 72.058 75.773265.501 251.82970.03 70.507500 72.025 75.804277.768 250.95869.955 70.507500 72.022 75.749279.945 250.07569.903 70.499500 72.019 75.693276.595 252.27869.844 70.473500 72.008 75.578271.458 249.37169.827 70.452500 71.969 75.499267.482 252.15669.825 70.451500 71.964 75.502266.207 250.16869.85 70.448500 71.961 75.51269.788 250.73369.814 70.442500 71.955 75.479268.994 252.15369.876 70.422500 71.928 75.517265.553 249.65869.929 70.405500 71.913 75.554250.64 253.04869.833 70.401500 71.909 75.533268.467 250.02269.817 70.398500 71.908 75.533277.008 251.98769.931 70.395500 71.908 75.533271.107 252.30469.962 70.396500 71.907 75.559257.13 250.11469.948 70.396500 71.905 75.622265.643 253.21169.954 70.395500 71.902 75.662270.249 249.30569.975 70.394500 71.899 75.685275.604 252.19869.916 70.395500 71.899 75.555272.934 251.0269.97 70.395500 71.898 75.568271.408 250.22270.005 70.396500 71.887 75.667271.532 252.57770.028 70.396500 71.894 75.65276.48 249.38969.993 70.395500 71.885 75.699Time:date,hh:mm:ss04/27/2010,12:17:4104/27/2010,12:18:4104/27/2010,12:19:4104/27/2010,12:20:4104/27/2010,12:21:4104/27/2010,12:22:4104/27/2010,12:23:4204/27/2010,12:24:4204/27/2010,12:25:4204/27/2010,12:26:4204/27/2010,12:27:4204/27/2010,12:28:4204/27/2010,12:29:4204/27/2010,12:30:4204/27/2010,12:31:4204/27/2010,12:32:4204/27/2010,12:33:4204/27/2010,12:34:4204/27/2010,12:35:4204/27/2010,12:36:4204/27/2010,12:37:4204/27/2010,12:38:4204/27/2010,12:39:4204/27/2010,12:40:4204/27/2010,12:41:4204/27/2010,12:42:4204/27/2010,12:43:4204/27/2010,12:44:4204/27/2010,12:45:4204/27/2010,12:46:4204/27/2010,12:47:4304/27/2010,12:48:4304/27/2010,12:49:4304/27/2010,12:50:4304/27/2010,12:51:43Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal79.433 629.384 584.271 654.458 622.24379.437 632.532 587.152 657.74 625.31979.442 635.606 589.981 660.946 628.33779.442 638.696 592.816 664.167 631.36379.445 641.809 595.708 667.413 634.4579.448 644.927 598.521 670.664 637.45179.451 647.998 601.394 673.867 640.51779.453 651.09 604.221 677.09 643.53479.456 654.249 607.075 680.383 646.57979.457 657.34 609.922 683.606 649.61679.46 660.432 612.796 686.829 652.68279.461 663.514 615.635 690.041 655.7179.461 666.677 618.468 693.338 658.73279.461 669.758 621.363 696.549 661.82179.463 672.85 624.178 699.773 664.82479.465 675.958 627.072 703.013 667.91179.465 679.116 629.892 706.304 670.9279.465 682.221 632.77 709.54 673.9979.466 685.338 635.624 712.79 677.03579.465 688.447 638.497 716.03 680.09979.464 691.625 641.36 719.343 683.15379.462 694.732 644.247 722.581 686.23279.461 697.844 647.098 725.825 689.27479.46 700.955 649.991 729.067 692.35979.456 704.124 652.842 732.37 695.479.452 707.218 655.707 735.595 698.45679.447 710.325 658.591 738.833 701.53279.442 713.439 661.412 742.079 704.54179.44 716.602 664.337 745.376 707.66279.434 719.713 667.16 748.618 710.67279.427 722.845 670.082 751.883 713.7979.423 725.968 672.906 755.138 716.80279.418 729.102 675.8 758.405 719.88979.41 732.239 678.636 761.675 722.91579.405 735.338 681.519 764.906 725.991Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,12:52:430 28.7890.888 2.952 0.984 3.032 00 186.43204/27/2010,12:53:430 28.7890.888 2.935 0.984 3.03 00 186.18804/27/2010,12:54:430 28.7870.888 2.728 0.984 3.028 00 186.27104/27/2010,12:55:430 28.7870.888 2.768 0.984 3.03 00 186.29504/27/2010,12:56:430 28.7860.888 2.991 0.984 3.031 00 186.15704/27/2010,12:57:430 28.7870.888 2.915 0.984 3.03 00 186.13804/27/2010,12:58:430 28.7880.888 2.871 0.985 3.033 00 186.02204/27/2010,12:59:430 28.790.888 2.827 0.985 3.035 00 185.89104/27/2010,13:00:43 Sampling complete 240.24655 Minutes sampledC:Drive Code:0Compact Flash Code:0Time:date,hh:mm:ss04/27/2010,12:52:4304/27/2010,12:53:4304/27/2010,12:54:4304/27/2010,12:55:4304/27/2010,12:56:4304/27/2010,12:57:4304/27/2010,12:58:4304/27/2010,12:59:4304/27/2010,13:00:43C:Drive Code:0Compact Flash Code:0Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.331 252.30769.82 70.363500 71.827 75.578268.449 250.38469.74 70.339500 71.779 75.509268.359 250.62669.764 70.339500 71.757 75.514261.888 252.24369.749 70.338500 71.76 75.506255.932 249.32669.684 70.339500 71.748 75.464237.171 252.67269.718 70.332500 71.752 75.486202.815 250.05169.695 70.332500 71.747 75.493187.984 251.85969.691 70.314500 71.757 75.505Time:date,hh:mm:ss04/27/2010,12:52:4304/27/2010,12:53:4304/27/2010,12:54:4304/27/2010,12:55:4304/27/2010,12:56:4304/27/2010,12:57:4304/27/2010,12:58:4304/27/2010,12:59:4304/27/2010,13:00:43C:Drive Code:0Compact Flash Code:0Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal79.398 738.46 684.373 768.161 729.03679.39 741.584 687.241 771.419 732.09679.385 744.747 690.11 774.716 735.15679.381 747.847 692.998 777.948 738.23779.373 750.962 695.843 781.196 741.27379.365 754.073 698.737 784.44 744.3679.355 757.243 701.59 787.745 747.40379.35 760.339 704.442 790.972 750.446Hg TESTPARAMETERS 4/27/2010 2:45 PMXducerPitotBarom Flow 1Vac 1 Flow 2 Vac 2 aux LoadGain1.12 3.410.17 1100 0.189 1100 10Offset0.001 17.40.004 0.5 0.004 0.5 00TstdPstdGam 1 Gam 2CPL 2 CPL 16829.92 1.00130.9812 526.106 526.211Prop timeProbe min Filter min Stack min Test time0.5225 250150 240LpmMotor V Log Time File Suffix Load Proportion0.82.6 60 South 4-27-10 r3 Pitot ManualTime:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,14:45:380 28.8270.872 3.682 0.745 3.395 00 184.27604/27/2010,14:46:380 28.8290.888 2.736 0.987 2.981 00 184.17104/27/2010,14:47:380 28.8290.888 2.78 0.987 2.885 00 184.13604/27/2010,14:48:380 28.8310.888 2.799 0.987 2.89 00 184.12904/27/2010,14:49:380 28.8310.888 2.721 0.987 2.891 00 184.17304/27/2010,14:50:380 28.8290.888 2.773 0.987 2.894 00 184.20304/27/2010,14:51:380 28.830.888 2.765 0.987 2.895 00 184.20904/27/2010,14:52:380 28.830.888 2.806 0.987 2.894 00 184.23704/27/2010,14:53:380 28.8310.888 2.593 0.987 2.897 00 184.25604/27/2010,14:54:390 28.8330.888 2.621 0.987 2.896 00 184.31704/27/2010,14:55:390 28.8370.888 2.719 0.987 2.899 00 184.29104/27/2010,14:56:390 28.8430.888 2.669 0.987 2.897 00 184.28504/27/2010,14:57:390 28.8480.888 2.879 0.987 2.901 00 184.26904/27/2010,14:58:390 28.8450.888 2.706 0.986 2.901 00 184.18204/27/2010,14:59:390 28.8470.888 2.715 0.986 2.897 00 184.05904/27/2010,15:00:390 28.8470.888 2.685 0.986 2.895 00 184.10704/27/2010,15:01:390 28.8530.888 2.717 0.986 2.896 00 184.25704/27/2010,15:02:390 28.8510.888 2.802 0.986 2.896 00 184.30304/27/2010,15:03:390 28.8470.888 2.764 0.986 2.895 00 184.27904/27/2010,15:04:390 28.8440.888 2.729 0.986 2.895 00 184.3604/27/2010,15:05:390 28.8420.888 2.818 0.986 2.891 00 184.39404/27/2010,15:06:390 28.8410.888 2.761 0.986 2.891 00 184.356Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,14:45:3804/27/2010,14:46:3804/27/2010,14:47:3804/27/2010,14:48:3804/27/2010,14:49:3804/27/2010,14:50:3804/27/2010,14:51:3804/27/2010,14:52:3804/27/2010,14:53:3804/27/2010,14:54:3904/27/2010,14:55:3904/27/2010,14:56:3904/27/2010,14:57:3904/27/2010,14:58:3904/27/2010,14:59:3904/27/2010,15:00:3904/27/2010,15:01:3904/27/2010,15:02:3904/27/2010,15:03:3904/27/2010,15:04:3904/27/2010,15:05:3904/27/2010,15:06:39Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF275.275 248.39864.629 66.553500 68.392 70.081275.116 251.71864.696 66.52500 68.392 70.175275.044 249.58164.74 66.477500 68.349 70.079274.94 250.19464.787 66.374500 68.254 70.148274.979 251.90964.71 66.342500 68.218 70.099275.003 248.79664.676 66.307500 68.181 70.021274.871 252.14364.637 66.256500 68.132 70.016275.023 250.15564.5 66.24500 68.114 69.948274.891 250.44464.423 66.195500 68.066 69.786274.726 252.28164.532 66.138500 68.026 69.799274.932 248.87664.652 66.079500 67.998 69.822274.74 252.34164.888 66.038500 67.921 70.089274.806 249.0765.081 66.047500 67.91 70.408274.75 250.50665.143 66.025500 67.877 70.556274.761 249.57565.164 66.004500 67.871 70.631274.741 249.19965.322 66.019500 67.863 70.738274.665 250.4265.443 65.984500 67.834 70.893274.668 249.15365.595 65.975500 67.823 71.096274.635 251.11265.65 65.965500 67.792 71.144274.655 249.6465.672 65.966500 67.807 71.2274.641 250.3365.666 65.934500 67.778 71.248274.717 250.6265.617 65.914500 67.762 71.28Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,14:45:3804/27/2010,14:46:3804/27/2010,14:47:3804/27/2010,14:48:3804/27/2010,14:49:3804/27/2010,14:50:3804/27/2010,14:51:3804/27/2010,14:52:3804/27/2010,14:53:3804/27/2010,14:54:3904/27/2010,14:55:3904/27/2010,14:56:3904/27/2010,14:57:3904/27/2010,14:58:3904/27/2010,14:59:3904/27/2010,15:00:3904/27/2010,15:01:3904/27/2010,15:02:3904/27/2010,15:03:3904/27/2010,15:04:3904/27/2010,15:05:3904/27/2010,15:06:39Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal76.465 2.954 2.282 3.054 2.41676.42 6.238 5.225 6.448 5.53176.373 9.539 8.314 9.859 8.80176.329 12.824 11.343 13.253 12.00576.285 16.118 14.4 16.657 15.2476.242 19.421 17.436 20.07 18.45376.199 22.714 20.514 23.472 21.70976.157 26.007 23.554 26.873 24.92576.117 29.302 26.582 30.277 28.12776.074 32.596 29.66 33.679 31.38376.032 35.899 32.68 37.088 34.57775.99 39.2 35.712 40.495 37.78175.951 42.498 38.762 43.899 41.00575.91 45.8 41.812 47.306 44.22975.871 49.094 44.832 50.706 47.4275.834 52.394 47.893 54.111 50.65575.798 55.699 50.973 57.521 53.90975.765 58.992 54.012 60.919 57.1275.732 62.291 57.03 64.322 60.30975.701 65.593 60.104 67.729 63.55875.669 68.885 63.135 71.127 66.7675.637 72.191 66.185 74.539 69.984Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,15:07:390 28.840.888 2.788 0.986 2.891 00 184.3404/27/2010,15:08:390 28.8410.888 2.664 0.986 2.891 00 184.25904/27/2010,15:09:390 28.8410.888 2.736 0.986 2.89 00 184.20804/27/2010,15:10:390 28.8410.888 2.741 0.986 2.894 00 183.99204/27/2010,15:11:390 28.8410.888 2.728 0.986 2.894 00 184.1204/27/2010,15:12:390 28.8410.888 2.768 0.986 2.891 00 184.14904/27/2010,15:13:390 28.8390.888 2.762 0.986 2.893 00 184.18604/27/2010,15:14:390 28.8390.888 2.803 0.986 2.893 00 184.14404/27/2010,15:15:390 28.8390.888 2.895 0.986 2.906 00 184.13804/27/2010,15:16:390 28.8390.888 2.993 0.986 2.987 00 184.15704/27/2010,15:17:390 28.8390.888 3.006 0.986 2.981 00 184.24604/27/2010,15:18:400 28.8390.888 2.833 0.986 2.983 00 184.29704/27/2010,15:19:400 28.8390.888 2.936 0.986 2.987 00 184.37904/27/2010,15:20:400 28.8390.888 2.848 0.986 2.989 00 184.38104/27/2010,15:21:400 28.8390.888 2.922 0.986 2.984 00 184.49204/27/2010,15:22:400 28.8390.888 2.831 0.986 2.985 00 184.68104/27/2010,15:23:400 28.8390.888 3.02 0.986 2.988 00 184.76104/27/2010,15:24:400 28.8380.888 2.926 0.986 2.989 00 184.81104/27/2010,15:25:400 28.8360.888 2.801 0.986 2.987 00 184.75404/27/2010,15:26:400 28.8350.888 2.948 0.986 2.989 00 184.69704/27/2010,15:27:400 28.8340.888 2.871 0.986 2.993 00 184.7204/27/2010,15:28:400 28.8340.888 2.945 0.986 2.995 00 184.84804/27/2010,15:29:400 28.8330.888 2.857 0.986 2.995 00 184.96604/27/2010,15:30:400 28.8310.888 2.832 0.986 2.996 00 185.32704/27/2010,15:31:400 28.830.888 2.865 0.986 2.994 00 184.86104/27/2010,15:32:400 28.8270.888 2.648 0.986 2.993 00 184.94704/27/2010,15:33:400 28.8270.888 2.863 0.986 2.997 00 185.02904/27/2010,15:34:400 28.8260.888 3.003 0.986 2.998 00 185.00304/27/2010,15:35:400 28.8260.888 2.938 0.986 2.997 00 184.97604/27/2010,15:36:400 28.8270.888 3.026 0.986 2.998 00 184.97404/27/2010,15:37:400 28.8280.888 2.996 0.986 2.996 00 185.02904/27/2010,15:38:400 28.8270.888 3.005 0.986 2.998 00 18504/27/2010,15:39:400 28.8260.888 2.782 0.986 2.996 00 184.96704/27/2010,15:40:400 28.8260.888 2.882 0.986 2.994 00 185.00204/27/2010,15:41:400 28.8270.888 3.101 0.986 2.997 00 185.005Time:date,hh:mm:ss04/27/2010,15:07:3904/27/2010,15:08:3904/27/2010,15:09:3904/27/2010,15:10:3904/27/2010,15:11:3904/27/2010,15:12:3904/27/2010,15:13:3904/27/2010,15:14:3904/27/2010,15:15:3904/27/2010,15:16:3904/27/2010,15:17:3904/27/2010,15:18:4004/27/2010,15:19:4004/27/2010,15:20:4004/27/2010,15:21:4004/27/2010,15:22:4004/27/2010,15:23:4004/27/2010,15:24:4004/27/2010,15:25:4004/27/2010,15:26:4004/27/2010,15:27:4004/27/2010,15:28:4004/27/2010,15:29:4004/27/2010,15:30:4004/27/2010,15:31:4004/27/2010,15:32:4004/27/2010,15:33:4004/27/2010,15:34:4004/27/2010,15:35:4004/27/2010,15:36:4004/27/2010,15:37:4004/27/2010,15:38:4004/27/2010,15:39:4004/27/2010,15:40:4004/27/2010,15:41:40Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.683 250.13565.595 65.898500 67.728 71.318274.841 251.20265.655 65.865500 67.65 71.338274.849 251.23865.73 65.867500 67.65 71.496274.724 250.25365.655 65.806500 67.609 71.423274.752 251.99165.74 65.825500 67.598 71.493274.779 251.05165.707 65.81500 67.59 71.502274.861 250.57765.709 65.744500 67.56 71.46274.796 252.26465.712 65.746500 67.58 71.479274.941 249.70965.698 65.706500 67.551 71.398274.839 252.03265.583 65.692500 67.537 71.278274.792 251.38965.554 65.697500 67.538 71.248274.845 250.44165.594 65.689500 67.499 71.214274.779 252.80965.61 65.685500 67.487 71.181274.886 250.22465.589 65.688500 67.515 71.261274.71 251.59565.631 65.66500 67.507 71.291274.723 252.07965.593 65.658500 67.489 71.134274.853 249.38165.607 65.683500 67.523 71.049274.504 252.38265.618 65.677500 67.527 70.991274.533 249.82965.618 65.656500 67.502 70.92274.753 251.23265.646 65.686500 67.533 70.912274.542 251.93565.706 65.695500 67.539 70.881274.548 249.65965.706 65.715500 67.568 70.803274.672 252.58665.665 65.689500 67.538 70.706274.601 250.31865.688 65.703500 67.561 70.684274.485 251.02465.726 65.74500 67.594 70.728274.614 252.41565.821 65.754500 67.608 70.75274.706 250.01865.88 65.798500 67.636 70.718274.546 252.81165.902 65.747500 67.608 70.696274.444 250.98365.92 65.807500 67.643 70.777274.59 251.08765.974 65.855500 67.673 70.762274.59 252.25866.01 65.886500 67.756 70.79274.547 249.44766.067 65.913500 67.782 70.792274.56 252.52466.187 65.943500 67.815 70.797274.405 249.86566.217 65.936500 67.804 70.826274.451 250.95766.223 65.954500 67.818 70.807Time:date,hh:mm:ss04/27/2010,15:07:3904/27/2010,15:08:3904/27/2010,15:09:3904/27/2010,15:10:3904/27/2010,15:11:3904/27/2010,15:12:3904/27/2010,15:13:3904/27/2010,15:14:3904/27/2010,15:15:3904/27/2010,15:16:3904/27/2010,15:17:3904/27/2010,15:18:4004/27/2010,15:19:4004/27/2010,15:20:4004/27/2010,15:21:4004/27/2010,15:22:4004/27/2010,15:23:4004/27/2010,15:24:4004/27/2010,15:25:4004/27/2010,15:26:4004/27/2010,15:27:4004/27/2010,15:28:4004/27/2010,15:29:4004/27/2010,15:30:4004/27/2010,15:31:4004/27/2010,15:32:4004/27/2010,15:33:4004/27/2010,15:34:4004/27/2010,15:35:4004/27/2010,15:36:4004/27/2010,15:37:4004/27/2010,15:38:4004/27/2010,15:39:4004/27/2010,15:40:4004/27/2010,15:41:40Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal75.608 75.491 69.228 77.944 73.275.579 78.787 72.312 81.346 76.45875.554 82.087 75.35 84.751 79.66875.528 85.394 78.383 88.162 82.87375.502 88.696 81.464 91.57 86.12775.475 92.009 84.484 94.989 89.31975.448 95.321 87.525 98.405 92.53175.425 98.615 90.578 101.803 95.75675.399 101.816 93.613 105.106 98.96375.375 104.946 96.541 108.335 102.05575.352 108.129 99.52 111.619 105.20375.327 111.246 102.426 114.834 108.27375.306 114.371 105.409 118.057 111.42475.286 117.48 108.29 121.265 114.46775.265 120.654 111.273 124.539 117.61975.246 123.755 114.197 127.738 120.70875.225 126.863 117.134 130.944 123.8175.205 130.024 120.093 134.205 126.93675.187 133.139 122.994 137.418 13075.17 136.259 125.94 140.638 133.11475.151 139.364 128.862 143.842 136.20175.134 142.534 131.803 147.112 139.30875.121 145.626 134.722 150.303 142.39375.104 148.729 137.667 153.505 145.50575.089 151.891 140.578 156.768 148.58275.074 155.001 143.531 159.978 151.70375.064 158.088 146.43 163.165 154.76775.051 161.211 149.393 166.388 157.975.038 164.344 152.281 169.622 160.95275.027 167.435 155.24 172.813 164.08175.016 170.533 158.14 176.011 167.14775.008 173.693 161.097 179.274 170.27475 176.77 163.969 182.452 173.31174.993 179.872 166.941 185.654 176.45374.985 183.035 169.826 188.92 179.504Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,15:42:410 28.8270.888 2.732 0.986 2.994 00 184.92804/27/2010,15:43:410 28.8250.888 2.848 0.986 2.997 00 184.91404/27/2010,15:44:410 28.8230.888 3.157 0.986 2.997 00 185.01904/27/2010,15:45:410 28.8210.888 2.835 0.986 2.999 00 185.04904/27/2010,15:46:410 28.820.888 2.774 0.986 3.001 00 185.19404/27/2010,15:47:410 28.8180.888 2.847 0.986 3.001 00 185.23604/27/2010,15:48:410 28.8170.888 2.971 0.986 3.005 00 185.20404/27/2010,15:49:410 28.8120.888 2.913 0.986 2.999 00 185.19804/27/2010,15:50:410 28.8090.888 2.909 0.986 3 00 185.20504/27/2010,15:51:410 28.8090.888 2.821 0.986 3.003 00 185.20804/27/2010,15:52:410 28.8080.888 3.052 0.986 3.003 00 185.10804/27/2010,15:53:410 28.8090.888 2.938 0.986 3.007 00 185.03804/27/2010,15:54:410 28.8090.888 2.959 0.986 3.002 00 185.04904/27/2010,15:55:410 28.810.888 2.966 0.986 3.005 00 185.1604/27/2010,15:56:410 28.8120.888 2.835 0.986 3.007 00 185.204/27/2010,15:57:410 28.8130.888 2.796 0.986 3.006 00 185.29304/27/2010,15:58:410 28.8130.888 2.859 0.986 3 00 185.14604/27/2010,15:59:410 28.8140.888 2.635 0.986 3.002 00 185.28404/27/2010,16:00:410 28.8150.888 2.838 0.986 3.005 00 185.39504/27/2010,16:01:410 28.8160.888 3.031 0.986 3.005 00 185.49704/27/2010,16:02:410 28.8170.888 3.118 0.986 3.002 00 185.44304/27/2010,16:03:410 28.8180.888 2.818 0.986 3.001 00 185.30804/27/2010,16:04:410 28.8180.888 2.963 0.986 2.996 00 185.45504/27/2010,16:05:410 28.8180.888 2.67 0.986 3.001 00 185.58704/27/2010,16:06:420 28.8170.888 2.895 0.986 3.001 00 185.57504/27/2010,16:07:420 28.8170.888 2.739 0.986 2.999 00 185.5304/27/2010,16:08:420 28.8170.888 2.847 0.986 3.001 00 185.49704/27/2010,16:09:420 28.8160.888 2.776 0.986 2.999 00 185.46304/27/2010,16:10:420 28.8150.888 2.859 0.986 3.001 00 185.43404/27/2010,16:11:420 28.8150.888 2.802 0.985 3.003 00 185.46904/27/2010,16:12:420 28.8150.888 2.731 0.985 3.007 00 185.47104/27/2010,16:13:420 28.8140.888 2.786 0.985 3.002 00 185.24104/27/2010,16:14:420 28.8150.888 2.808 0.985 2.999 00 185.31604/27/2010,16:15:420 28.8160.888 2.809 0.985 2.999 00 185.44604/27/2010,16:16:420 28.8170.888 2.694 0.985 3.002 00 185.336Time:date,hh:mm:ss04/27/2010,15:42:4104/27/2010,15:43:4104/27/2010,15:44:4104/27/2010,15:45:4104/27/2010,15:46:4104/27/2010,15:47:4104/27/2010,15:48:4104/27/2010,15:49:4104/27/2010,15:50:4104/27/2010,15:51:4104/27/2010,15:52:4104/27/2010,15:53:4104/27/2010,15:54:4104/27/2010,15:55:4104/27/2010,15:56:4104/27/2010,15:57:4104/27/2010,15:58:4104/27/2010,15:59:4104/27/2010,16:00:4104/27/2010,16:01:4104/27/2010,16:02:4104/27/2010,16:03:4104/27/2010,16:04:4104/27/2010,16:05:4104/27/2010,16:06:4204/27/2010,16:07:4204/27/2010,16:08:4204/27/2010,16:09:4204/27/2010,16:10:4204/27/2010,16:11:4204/27/2010,16:12:4204/27/2010,16:13:4204/27/2010,16:14:4204/27/2010,16:15:4204/27/2010,16:16:42Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.514 251.33666.255 65.974500 67.849 70.923274.431 249.6466.305 66.012500 67.873 70.973274.529 252.61666.364 66.03500 67.891 70.93274.54 250.14766.467 66.067500 67.928 70.986274.421 251.55166.529 66.094500 67.951 71.051274.523 252.27366.552 66.169500 68.034 71.063274.495 249.96566.599 66.197500 68.048 71.102274.438 253.19166.588 66.24500 68.084 71.127274.483 250.35966.585 66.254500 68.098 71.133274.545 251.87866.584 66.286500 68.101 71.145274.542 252.71866.595 66.306500 68.136 71.182274.466 250.29466.591 66.315500 68.151 71.181274.629 253.89166.624 66.358500 68.156 71.335274.733 250.88866.64 66.361500 68.157 71.377274.51 252.47666.681 66.398500 68.177 71.519274.614 253.19566.708 66.46500 68.203 71.558274.682 250.51966.784 66.473500 68.209 71.624274.438 253.98266.825 66.487500 68.211 71.624274.559 250.85866.886 66.522500 68.241 71.66274.662 252.37266.921 66.533500 68.265 71.676274.569 252.40467.013 66.608500 68.364 71.787274.46 249.51667.029 66.64500 68.417 71.793274.493 252.75567.052 66.653500 68.434 71.817274.61 248.71767.141 66.69500 68.442 71.906274.387 251.68667.194 66.703500 68.479 72.008274.408 249.88167.184 66.733500 68.49 72.114274.483 249.88967.197 66.799500 68.498 72.12274.484 251.73167.213 66.81500 68.519 72.146274.402 249.06367.229 66.835500 68.556 72.188274.554 251.95467.301 66.913500 68.659 72.229274.521 250.06467.326 66.921500 68.659 72.238274.346 25067.362 66.942500 68.67 72.236274.352 251.78567.427 66.97500 68.698 72.257274.475 248.48867.48 66.979500 68.711 72.287274.454 252.00967.518 66.998500 68.717 72.264Time:date,hh:mm:ss04/27/2010,15:42:4104/27/2010,15:43:4104/27/2010,15:44:4104/27/2010,15:45:4104/27/2010,15:46:4104/27/2010,15:47:4104/27/2010,15:48:4104/27/2010,15:49:4104/27/2010,15:50:4104/27/2010,15:51:4104/27/2010,15:52:4104/27/2010,15:53:4104/27/2010,15:54:4104/27/2010,15:55:4104/27/2010,15:56:4104/27/2010,15:57:4104/27/2010,15:58:4104/27/2010,15:59:4104/27/2010,16:00:4104/27/2010,16:01:4104/27/2010,16:02:4104/27/2010,16:03:4104/27/2010,16:04:4104/27/2010,16:05:4104/27/2010,16:06:4204/27/2010,16:07:4204/27/2010,16:08:4204/27/2010,16:09:4204/27/2010,16:10:4204/27/2010,16:11:4204/27/2010,16:12:4204/27/2010,16:13:4204/27/2010,16:14:4204/27/2010,16:15:4204/27/2010,16:16:42Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal74.978 186.138 172.782 192.124 182.6374.974 189.228 175.69 195.315 185.70674.968 192.35 178.618 198.54 188.80274.964 195.465 181.548 201.757 191.90274.96 198.566 184.45 204.962 194.97274.959 201.652 187.39 208.15 198.08474.959 204.792 190.278 211.394 201.1474.959 207.853 193.229 214.558 204.26374.959 210.959 196.112 217.77 207.31674.959 214.106 199.057 221.024 210.43374.959 217.169 201.943 224.19 213.48974.959 220.249 204.875 227.375 216.59374.961 223.405 207.773 230.638 219.66174.964 226.474 210.69 233.811 222.7574.968 229.555 213.597 236.996 225.82774.972 232.688 216.509 240.236 228.9174.976 235.776 219.421 243.429 231.99374.978 238.852 222.345 246.61 235.0974.984 241.969 225.252 249.833 238.16774.99 245.054 228.173 253.024 241.25974.996 248.143 231.083 256.219 244.3475.001 251.25 234.01 259.432 247.44175.008 254.357 236.916 262.646 250.51875.012 257.457 239.847 265.852 253.62275.021 260.545 242.749 269.046 256.69575.029 263.689 245.688 272.298 259.80975.038 266.751 248.578 275.466 262.86975.048 269.853 251.531 278.675 265.99875.057 273.001 254.413 281.933 269.0575.067 276.075 257.371 285.114 272.18575.075 279.164 260.241 288.31 275.22675.085 282.298 263.189 291.554 278.34975.098 285.39 266.077 294.754 281.40975.11 288.479 269.031 297.951 284.5475.123 291.584 271.905 301.164 287.585Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,16:17:420 28.8180.888 3.022 0.985 2.998 00 185.16504/27/2010,16:18:420 28.8190.888 2.815 0.985 3 00 185.15804/27/2010,16:19:420 28.820.888 3.131 0.985 2.999 00 185.03204/27/2010,16:20:420 28.820.888 2.932 0.985 2.999 00 184.94304/27/2010,16:21:420 28.8210.888 2.811 0.985 3 00 184.90504/27/2010,16:22:420 28.8230.888 2.658 0.985 3 00 184.89804/27/2010,16:23:420 28.8240.888 2.894 0.985 3 00 184.74904/27/2010,16:24:420 28.8250.888 3.22 0.985 2.996 00 184.66304/27/2010,16:25:420 28.8270.888 2.868 0.985 3.001 00 184.73504/27/2010,16:26:420 28.8280.888 2.946 0.985 3.001 00 184.73104/27/2010,16:27:420 28.8290.888 2.807 0.985 3.003 00 184.75304/27/2010,16:28:420 28.8290.888 2.947 0.985 3.004 00 184.74304/27/2010,16:29:420 28.830.888 3.053 0.985 3.003 00 184.73604/27/2010,16:30:420 28.8310.888 2.797 0.985 3.003 00 184.79204/27/2010,16:31:430 28.8310.888 2.9 0.985 3.001 00 184.74804/27/2010,16:32:430 28.8320.888 2.864 0.985 3 00 184.72604/27/2010,16:33:430 28.8340.888 2.955 0.985 3.002 00 185.11504/27/2010,16:34:430 28.8360.888 2.999 0.985 2.999 00 184.76404/27/2010,16:35:430 28.8380.888 2.904 0.985 2.997 00 184.50204/27/2010,16:36:430 28.8390.888 2.911 0.985 3.001 00 184.78804/27/2010,16:37:430 28.840.888 2.896 0.985 3.002 00 184.83704/27/2010,16:38:430 28.840.888 2.892 0.985 2.996 00 184.77304/27/2010,16:39:430 28.8390.888 2.888 0.985 2.998 00 184.87704/27/2010,16:40:430 28.840.888 2.847 0.985 2.999 00 184.76304/27/2010,16:41:430 28.8410.888 2.899 0.985 2.997 00 184.77904/27/2010,16:42:430 28.8420.888 2.965 0.985 2.998 00 184.88504/27/2010,16:43:430 28.8440.888 2.826 0.985 2.996 00 184.88204/27/2010,16:44:430 28.8450.888 2.978 0.985 3.001 00 184.96204/27/2010,16:45:430 28.8460.888 2.832 0.985 3.001 00 184.76804/27/2010,16:46:430 28.8470.888 2.926 0.985 2.999 00 184.80604/27/2010,16:47:430 28.8470.888 2.62 0.985 2.999 00 184.77204/27/2010,16:48:430 28.8470.888 2.934 0.985 3.003 00 184.70104/27/2010,16:49:430 28.8470.888 2.74 0.985 3.003 00 184.70504/27/2010,16:50:430 28.8480.888 2.787 0.985 3.002 00 184.75904/27/2010,16:51:430 28.850.888 2.961 0.985 2.998 00 184.905Time:date,hh:mm:ss04/27/2010,16:17:4204/27/2010,16:18:4204/27/2010,16:19:4204/27/2010,16:20:4204/27/2010,16:21:4204/27/2010,16:22:4204/27/2010,16:23:4204/27/2010,16:24:4204/27/2010,16:25:4204/27/2010,16:26:4204/27/2010,16:27:4204/27/2010,16:28:4204/27/2010,16:29:4204/27/2010,16:30:4204/27/2010,16:31:4304/27/2010,16:32:4304/27/2010,16:33:4304/27/2010,16:34:4304/27/2010,16:35:4304/27/2010,16:36:4304/27/2010,16:37:4304/27/2010,16:38:4304/27/2010,16:39:4304/27/2010,16:40:4304/27/2010,16:41:4304/27/2010,16:42:4304/27/2010,16:43:4304/27/2010,16:44:4304/27/2010,16:45:4304/27/2010,16:46:4304/27/2010,16:47:4304/27/2010,16:48:4304/27/2010,16:49:4304/27/2010,16:50:4304/27/2010,16:51:43Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.331 248.90467.613 67.115500 68.775 72.32274.276 250.70167.654 67.146500 68.822 72.342274.43 250.65967.723 67.159500 68.825 72.327274.521 248.9567.76 67.194500 68.826 72.35274.215 251.71367.754 67.202500 68.839 72.389274.218 248.99567.848 67.262500 68.939 72.551274.321 251.48567.878 67.302500 68.989 72.635274.257 250.64667.956 67.314500 68.995 72.615274.252 249.83568.038 67.319500 68.999 72.644274.349 252.42768.142 67.427500 69.067 72.824274.255 248.94668.159 67.484500 69.105 72.904274.176 252.29868.205 67.499500 69.11 72.97274.257 249.94268.258 67.534500 69.135 73.013274.181 250.6268.382 67.595500 69.214 73.142274.119 252.13668.451 67.636500 69.219 73.209274.113 249.04568.486 67.652500 69.272 73.29274.187 252.3768.581 67.738500 69.358 73.347274.146 249.72468.652 67.817500 69.388 73.446274.058 250.78668.677 67.828500 69.422 73.502274.269 251.90268.743 67.898500 69.48 73.543274.235 249.03268.792 67.93500 69.501 73.654273.963 252.368.833 67.959500 69.524 73.789274.201 249.63468.99 68.083500 69.65 73.874274.26 250.95568.989 68.098500 69.668 73.912274.153 251.95469.023 68.125500 69.69 73.926274.272 249.41369.066 68.201500 69.759 73.948274.077 252.81469.101 68.21500 69.779 74.013274.108 249.93869.148 68.253500 69.817 74.148274.219 251.43169.189 68.312500 69.857 74.149274.24 252.32269.219 68.395500 69.941 74.213274.143 249.53769.336 68.434500 70.003 74.337274.147 253.12169.336 68.445500 70.008 74.343274.31 249.7869.397 68.525500 70.075 74.358274.039 251.65269.43 68.542500 70.099 74.326274.14 252.00269.535 68.632500 70.158 74.468Time:date,hh:mm:ss04/27/2010,16:17:4204/27/2010,16:18:4204/27/2010,16:19:4204/27/2010,16:20:4204/27/2010,16:21:4204/27/2010,16:22:4204/27/2010,16:23:4204/27/2010,16:24:4204/27/2010,16:25:4204/27/2010,16:26:4204/27/2010,16:27:4204/27/2010,16:28:4204/27/2010,16:29:4204/27/2010,16:30:4204/27/2010,16:31:4304/27/2010,16:32:4304/27/2010,16:33:4304/27/2010,16:34:4304/27/2010,16:35:4304/27/2010,16:36:4304/27/2010,16:37:4304/27/2010,16:38:4304/27/2010,16:39:4304/27/2010,16:40:4304/27/2010,16:41:4304/27/2010,16:42:4304/27/2010,16:43:4304/27/2010,16:44:4304/27/2010,16:45:4304/27/2010,16:46:4304/27/2010,16:47:4304/27/2010,16:48:4304/27/2010,16:49:4304/27/2010,16:50:4304/27/2010,16:51:43Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal75.133 294.701 274.861 304.391 290.71775.146 297.785 277.723 307.584 293.75175.161 300.868 280.685 310.775 296.88975.176 304.005 283.567 314.022 299.94375.189 307.071 286.509 317.196 303.06175.204 310.171 289.41 320.406 306.13675.221 313.319 292.334 323.665 309.23475.238 316.395 295.259 326.85 312.33475.254 319.479 298.16 330.043 315.4175.27 322.612 301.094 333.286 318.51975.288 325.703 303.978 336.487 321.57675.305 328.788 306.923 339.681 324.69775.322 331.897 309.802 342.9 327.7575.342 335.018 312.741 346.133 330.86575.364 338.093 315.628 349.318 333.92575.382 341.183 318.554 352.518 337.02775.405 344.333 321.456 355.781 340.10475.428 347.401 324.38 358.959 343.20575.448 350.481 327.292 362.149 346.29175.473 353.644 330.215 365.426 349.39275.498 356.731 333.121 368.624 352.47375.521 359.811 336.052 371.815 355.5875.546 362.928 338.953 375.045 358.65875.569 366.046 341.892 378.276 361.77575.594 369.13 344.783 381.472 364.84175.623 372.218 347.741 384.673 367.97975.647 375.377 350.615 387.947 371.02875.68 378.443 353.572 391.124 374.16475.707 381.532 356.45 394.327 377.21775.735 384.678 359.402 397.588 380.34975.765 387.771 362.259 400.794 383.38175.793 390.843 365.217 403.979 386.51975.825 393.951 368.079 407.202 389.55675.853 397.063 371.031 410.429 392.68975.885 400.148 373.918 413.627 395.753Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,16:52:430 28.8510.888 2.808 0.985 2.998 00 184.8904/27/2010,16:53:430 28.8520.888 2.741 0.985 2.999 00 184.94704/27/2010,16:54:430 28.8540.888 2.84 0.985 3.002 00 185.03304/27/2010,16:55:440 28.8550.888 3.014 0.985 3.001 00 185.12904/27/2010,16:56:440 28.8570.888 2.947 0.985 3.001 00 185.20704/27/2010,16:57:440 28.8590.888 2.914 0.985 3.002 00 185.1304/27/2010,16:58:440 28.860.888 2.946 0.985 2.997 00 185.16904/27/2010,16:59:440 28.8610.888 3.247 0.985 3.004 00 185.22304/27/2010,17:00:440 28.8610.888 2.997 0.985 2.994 00 185.29804/27/2010,17:01:440 28.8620.888 2.86 0.985 2.996 00 185.23904/27/2010,17:02:440 28.8620.888 2.89 0.985 2.996 00 185.28804/27/2010,17:03:440 28.8620.888 3.217 0.985 2.994 00 185.29904/27/2010,17:04:440 28.8620.888 3.012 0.985 3.002 00 185.40304/27/2010,17:05:440 28.8620.888 3.019 0.985 2.998 00 185.47804/27/2010,17:06:440 28.8630.888 2.77 0.985 2.995 00 185.33704/27/2010,17:07:440 28.8640.888 2.859 0.985 2.995 00 185.33904/27/2010,17:08:440 28.8650.888 2.998 0.985 3 00 185.34404/27/2010,17:09:440 28.8660.888 2.813 0.985 3.002 00 185.30604/27/2010,17:10:440 28.8670.888 2.97 0.985 2.997 00 185.31304/27/2010,17:11:440 28.8690.888 2.949 0.985 2.995 00 185.24804/27/2010,17:12:440 28.870.888 2.689 0.985 3.001 00 185.14404/27/2010,17:13:440 28.8710.888 3.009 0.985 3 00 185.11304/27/2010,17:14:440 28.8720.888 2.874 0.985 3.002 00 185.20604/27/2010,17:15:440 28.8720.888 2.883 0.985 3.001 00 185.29704/27/2010,17:16:440 28.8730.888 2.93 0.985 2.996 00 185.29104/27/2010,17:17:440 28.8740.888 2.899 0.985 2.995 00 185.26104/27/2010,17:18:440 28.8750.888 2.874 0.985 2.997 00 185.37804/27/2010,17:19:450 28.8760.888 2.805 0.985 2.995 00 185.27204/27/2010,17:20:450 28.8760.888 3.087 0.985 2.997 00 185.30704/27/2010,17:21:450 28.8760.888 2.846 0.985 2.996 00 185.31304/27/2010,17:22:450 28.8760.888 2.932 0.985 2.994 00 185.35604/27/2010,17:23:450 28.8760.888 2.82 0.985 2.998 00 185.37604/27/2010,17:24:450 28.8770.888 2.886 0.985 2.998 00 185.4104/27/2010,17:25:450 28.8770.888 2.911 0.985 2.996 00 185.37304/27/2010,17:26:450 28.8780.888 3.133 0.985 3 00 185.365Time:date,hh:mm:ss04/27/2010,16:52:4304/27/2010,16:53:4304/27/2010,16:54:4304/27/2010,16:55:4404/27/2010,16:56:4404/27/2010,16:57:4404/27/2010,16:58:4404/27/2010,16:59:4404/27/2010,17:00:4404/27/2010,17:01:4404/27/2010,17:02:4404/27/2010,17:03:4404/27/2010,17:04:4404/27/2010,17:05:4404/27/2010,17:06:4404/27/2010,17:07:4404/27/2010,17:08:4404/27/2010,17:09:4404/27/2010,17:10:4404/27/2010,17:11:4404/27/2010,17:12:4404/27/2010,17:13:4404/27/2010,17:14:4404/27/2010,17:15:4404/27/2010,17:16:4404/27/2010,17:17:4404/27/2010,17:18:4404/27/2010,17:19:4504/27/2010,17:20:4504/27/2010,17:21:4504/27/2010,17:22:4504/27/2010,17:23:4504/27/2010,17:24:4504/27/2010,17:25:4504/27/2010,17:26:45Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.338 249.71269.554 68.661500 70.176 74.511274.095 252.99269.606 68.718500 70.241 74.513274.087 249.63169.617 68.766500 70.306 74.523274.19 251.83269.642 68.789500 70.343 74.518274.249 251.6869.772 68.83500 70.395 74.638274.206 249.86269.778 68.884500 70.416 74.719274.137 253.01869.828 68.98500 70.453 74.844274.164 249.59969.893 69.005500 70.47 74.898274.102 252.3569.998 69.051500 70.545 75.036274.174 251.22770.049 69.061500 70.594 75.082274.367 250.44470.083 69.121500 70.672 75.175274.107 253.06870.096 69.152500 70.681 75.188274.18 249.47970.139 69.204500 70.732 75.221274.361 252.83270.204 69.227500 70.739 75.243274.302 250.93670.286 69.327500 70.788 75.345274.105 250.88870.297 69.341500 70.798 75.312274.352 252.88470.371 69.386500 70.846 75.421274.422 249.66970.34569.4500 70.867 75.399274.232 253.21470.343 69.444500 70.956 75.518274.34 250.64970.367 69.455500 70.965 75.521274.371 251.2370.407 69.509500 71.012 75.608274.121 252.68470.454 69.535500 71.02 75.584274.34 249.67770.504 69.627500 71.068 75.619274.349 253.05870.514 69.653500 71.083 75.685274.223 250.4970.502 69.704500 71.124 75.693274.206 251.16670.492 69.724500 71.133 75.708274.298 252.04370.509 69.76500 71.169 75.737274.37 249.18370.465 69.754500 71.153 75.774274.345 252.95670.542 69.792500 71.198 75.886274.344 249.30670.516 69.785500 71.184 75.922274.341 251.73470.505 69.827500 71.271 75.952274.404 251.52970.453 69.835500 71.272 75.951274.51 249.69370.463 69.917500 71.281 75.984274.307 252.95970.395 69.912500 71.294 75.951274.43 249.48370.419 69.925500 71.319 75.966Time:date,hh:mm:ss04/27/2010,16:52:4304/27/2010,16:53:4304/27/2010,16:54:4304/27/2010,16:55:4404/27/2010,16:56:4404/27/2010,16:57:4404/27/2010,16:58:4404/27/2010,16:59:4404/27/2010,17:00:4404/27/2010,17:01:4404/27/2010,17:02:4404/27/2010,17:03:4404/27/2010,17:04:4404/27/2010,17:05:4404/27/2010,17:06:4404/27/2010,17:07:4404/27/2010,17:08:4404/27/2010,17:09:4404/27/2010,17:10:4404/27/2010,17:11:4404/27/2010,17:12:4404/27/2010,17:13:4404/27/2010,17:14:4404/27/2010,17:15:4404/27/2010,17:16:4404/27/2010,17:17:4404/27/2010,17:18:4404/27/2010,17:19:4504/27/2010,17:20:4504/27/2010,17:21:4504/27/2010,17:22:4504/27/2010,17:23:4504/27/2010,17:24:4504/27/2010,17:25:4504/27/2010,17:26:45Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal75.915 403.228 376.848 416.821 398.86375.947 406.382 379.756 420.092 401.94975.978 409.446 382.661 423.269 405.03276.006 412.539 385.587 426.477 408.13876.04 415.683 388.48 429.738 411.2176.071 418.772 391.417 432.942 414.32776.106 421.85 394.3 436.135 417.38776.138 424.957 397.233 439.358 420.50176.169 428.077 400.132 442.594 423.57876.202 431.151 403.05 445.783 426.67676.236 434.254 405.962 449.002 429.76976.271 437.408 408.894 452.275 432.88276.304 440.475 411.792 455.458 435.9676.34 443.561 414.722 458.66 439.07176.372 446.69 417.619 461.908 442.14976.407 449.781 420.574 465.116 445.28776.441 452.886 423.446 468.339 448.33776.475 455.971 426.399 471.541 451.47476.509 459.113 429.28 474.802 454.53476.542 462.186 432.231 477.991 457.66876.579 465.267 435.09 481.189 460.70676.612 468.416 438.045 484.458 463.84476.646 471.504 440.918 487.664 466.89676.68 474.581 443.855 490.858 470.01676.712 477.691 446.76 494.087 473.10276.746 480.806 449.677 497.321 476.20176.776 483.881 452.602 500.514 479.30876.808 486.98 455.497 503.731 482.38476.843 490.139 458.436 507.011 485.50776.874 493.223 461.326 510.214 488.57676.906 496.306 464.249 513.416 491.68276.938 499.427 467.159 516.656 494.77576.966 502.532 470.084 519.881 497.88376.996 505.623 472.986 523.091 500.96677.027 508.708 475.916 526.295 504.079Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,17:27:450 28.8790.888 2.906 0.985 2.994 00 185.27404/27/2010,17:28:450 28.8790.888 2.899 0.985 2.996 00 185.39904/27/2010,17:29:450 28.8790.888 2.902 0.985 2.998 00 185.37704/27/2010,17:30:450 28.880.888 2.888 0.985 2.996 00 185.2404/27/2010,17:31:450 28.880.888 2.908 0.985 2.998 00 185.22804/27/2010,17:32:450 28.880.888 2.897 0.985 3 00 185.25404/27/2010,17:33:450 28.880.888 2.894 0.985 2.995 00 185.15604/27/2010,17:34:450 28.880.888 2.9 0.985 2.997 00 185.08204/27/2010,17:35:450 28.8810.888 2.897 0.985 2.995 00 185.11604/27/2010,17:36:450 28.8820.888 2.889 0.985 3.002 00 185.42504/27/2010,17:37:450 28.8820.888 2.899 0.985 2.993 00 185.38704/27/2010,17:38:450 28.8810.888 2.894 0.985 2.996 00 185.00104/27/2010,17:39:450 28.8820.888 2.898 0.985 3 00 185.17404/27/2010,17:40:450 28.8810.888 2.891 0.985 2.999 00 185.20904/27/2010,17:41:450 28.8810.888 2.905 0.985 2.998 00 185.21504/27/2010,17:42:450 28.8810.888 2.908 0.985 2.998 00 185.30204/27/2010,17:43:460 28.8810.888 2.902 0.985 2.995 00 185.30104/27/2010,17:44:460 28.8820.888 2.91 0.985 2.996 00 185.23804/27/2010,17:45:460 28.8820.888 2.894 0.985 2.999 00 185.26304/27/2010,17:46:460 28.8820.888 2.906 0.985 2.997 00 185.24204/27/2010,17:47:460 28.8810.888 2.908 0.985 2.995 00 185.2704/27/2010,17:48:460 28.880.888 2.897 0.985 3 00 185.22904/27/2010,17:49:460 28.8790.888 2.947 0.985 2.998 00 185.22304/27/2010,17:50:460 28.8790.888 2.914 0.985 2.999 00 185.21104/27/2010,17:51:460 28.8780.888 2.789 0.985 3.001 00 185.29804/27/2010,17:52:460 28.8770.888 2.793 0.985 2.995 00 185.17204/27/2010,17:53:460 28.8770.888 2.829 0.985 2.995 00 185.1704/27/2010,17:54:460 28.8760.888 2.931 0.985 2.999 00 185.1504/27/2010,17:55:460 28.8770.888 2.848 0.985 2.998 00 185.1904/27/2010,17:56:460 28.8770.888 3.008 0.985 2.996 00 185.19704/27/2010,17:57:460 28.8770.888 3.143 0.985 2.999 00 185.06304/27/2010,17:58:460 28.8780.888 2.822 0.985 3 00 185.17404/27/2010,17:59:460 28.8780.888 3.109 0.985 3 00 185.1404/27/2010,18:00:460 28.8790.888 2.805 0.985 2.995 00 185.1904/27/2010,18:01:460 28.8790.888 2.776 0.985 2.996 00 185.26Time:date,hh:mm:ss04/27/2010,17:27:4504/27/2010,17:28:4504/27/2010,17:29:4504/27/2010,17:30:4504/27/2010,17:31:4504/27/2010,17:32:4504/27/2010,17:33:4504/27/2010,17:34:4504/27/2010,17:35:4504/27/2010,17:36:4504/27/2010,17:37:4504/27/2010,17:38:4504/27/2010,17:39:4504/27/2010,17:40:4504/27/2010,17:41:4504/27/2010,17:42:4504/27/2010,17:43:4604/27/2010,17:44:4604/27/2010,17:45:4604/27/2010,17:46:4604/27/2010,17:47:4604/27/2010,17:48:4604/27/2010,17:49:4604/27/2010,17:50:4604/27/2010,17:51:4604/27/2010,17:52:4604/27/2010,17:53:4604/27/2010,17:54:4604/27/2010,17:55:4604/27/2010,17:56:4604/27/2010,17:57:4604/27/2010,17:58:4604/27/2010,17:59:4604/27/2010,18:00:4604/27/2010,18:01:46Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.487 252.08870.434 69.949500 71.323 76.075274.448 251.31370.404 69.952500 71.304 75.972274.429 250.01770.441 70.002500 71.348 76.017274.41 252.94270.432 69.983500 71.339 75.995274.566 249.50370.415 70.004500 71.345 76.002274.496 252.34170.448 70.004500 71.349 75.943274.382 251.13870.448 70.021500 71.366 75.907274.376 250.2570.438 70.057500 71.397 75.9274.448 252.77570.396 70.056500 71.37 75.867274.549 249.30470.442 70.069500 71.38 75.874274.386 252.5970.503 70.071500 71.403 75.911274.418 250.85570.454 70.063500 71.399 75.83274.485 250.66970.457 70.096500 71.442 75.807274.465 252.91370.448 70.115500 71.425 75.811274.473 249.32670.434 70.108500 71.41 75.818274.364 252.59470.501 70.15500 71.514 75.871274.444 250.570.501 70.134500 71.514 75.858274.486 250.69770.489 70.13500 71.503 75.851274.456 252.58370.504 70.175500 71.544 75.856274.45 249.44570.471 70.171500 71.525 75.842274.402 252.85370.441 70.171500 71.517 75.895274.418 250.93570.471 70.263500 71.565 76.034274.408 251.2470.602 70.277500 71.571 76.114274.383 253.01570.576 70.273500 71.569 76.107274.54 249.86570.637 70.316500 71.603 76.055274.446 252.94870.621 70.322500 71.612 76.037274.411 250.61370.635 70.318500 71.604 75.936274.525 251.09270.645 70.336500 71.62 76.024274.471 252.51870.638 70.349500 71.633 76.053274.491 249.45770.664 70.346500 71.631 76.053274.483 252.90870.624 70.339500 71.629 76.069274.536 250.4170.679 70.392500 71.682 76.131274.51 250.67870.712 70.395500 71.684 76.208274.362 250.60970.717 70.395500 71.683 76.235274.467 249.38370.774 70.41500 71.697 76.282Time:date,hh:mm:ss04/27/2010,17:27:4504/27/2010,17:28:4504/27/2010,17:29:4504/27/2010,17:30:4504/27/2010,17:31:4504/27/2010,17:32:4504/27/2010,17:33:4504/27/2010,17:34:4504/27/2010,17:35:4504/27/2010,17:36:4504/27/2010,17:37:4504/27/2010,17:38:4504/27/2010,17:39:4504/27/2010,17:40:4504/27/2010,17:41:4504/27/2010,17:42:4504/27/2010,17:43:4604/27/2010,17:44:4604/27/2010,17:45:4604/27/2010,17:46:4604/27/2010,17:47:4604/27/2010,17:48:4604/27/2010,17:49:4604/27/2010,17:50:4604/27/2010,17:51:4604/27/2010,17:52:4604/27/2010,17:53:4604/27/2010,17:54:4604/27/2010,17:55:4604/27/2010,17:56:4604/27/2010,17:57:4604/27/2010,17:58:4604/27/2010,17:59:4604/27/2010,18:00:4604/27/2010,18:01:46Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal77.055 511.872 478.812 529.58 507.15677.084 514.937 481.765 532.763 510.29577.114 518.027 484.64 535.973 513.34977.141 521.156 487.602 539.223 516.49777.168 524.241 490.477 542.427 519.55177.197 527.343 493.425 545.648 522.68477.225 530.429 496.294 548.854 525.73277.249 533.572 499.24 552.119 528.86377.276 536.648 502.147 555.313 531.95277.302 539.744 505.056 558.529 535.04277.328 542.882 507.989 561.788 538.1677.35 545.97 510.88 564.996 541.23177.373 549.071 513.817 568.217 544.35277.398 552.159 516.704 571.425 547.4277.422 555.304 519.62 574.692 550.51877.444 558.379 522.529 577.886 553.61177.468 561.471 525.457 581.098 556.72277.493 564.612 528.363 584.361 559.81177.516 567.7 531.291 587.568 562.92377.538 570.795 534.186 590.784 56677.558 573.887 537.137 593.996 569.13677.58 577.03 540.016 597.262 572.19677.602 580.103 542.973 600.455 575.3477.624 583.195 545.846 603.668 578.39577.645 586.338 548.796 606.935 581.53177.663 589.423 551.66 610.141 584.57677.683 592.513 554.612 613.353 587.71477.703 595.611 557.508 616.572 590.79377.724 598.754 560.422 619.839 593.89277.744 601.818 563.357 623.024 597.01377.765 604.915 566.239 626.243 600.07777.781 608.062 569.178 629.514 603.20277.8 611.146 572.065 632.72 606.27177.82 614.247 574.982 635.943 609.37377.839 617.342 577.894 639.16 612.47Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,18:02:460 28.8790.888 2.961 0.985 2.999 00 185.33404/27/2010,18:03:460 28.8790.888 2.779 0.985 2.993 00 185.3704/27/2010,18:04:460 28.8790.888 2.853 0.985 2.996 00 185.36504/27/2010,18:05:460 28.8790.888 2.922 0.985 2.996 00 185.43804/27/2010,18:06:460 28.8780.888 3.009 0.985 2.995 00 185.46404/27/2010,18:07:460 28.8780.888 3.29 0.985 2.997 00 185.41304/27/2010,18:08:470 28.8790.888 2.811 0.985 2.995 00 185.36604/27/2010,18:09:470 28.8790.888 2.992 0.985 2.997 00 185.44304/27/2010,18:10:470 28.8790.888 2.981 0.985 2.992 00 185.51204/27/2010,18:11:470 28.8790.888 2.833 0.985 2.993 00 185.73904/27/2010,18:12:470 28.8790.888 2.896 0.985 2.995 00 185.88604/27/2010,18:13:470 28.880.888 2.98 0.985 2.993 00 185.98604/27/2010,18:14:470 28.880.888 2.667 0.985 2.995 00 185.99304/27/2010,18:15:470 28.8810.888 2.988 0.985 2.996 00 186.0704/27/2010,18:16:470 28.8820.888 2.998 0.985 2.997 00 186.32104/27/2010,18:17:470 28.8830.888 3.014 0.985 2.999 00 186.31304/27/2010,18:18:470 28.8840.888 2.937 0.985 2.997 00 186.33304/27/2010,18:19:470 28.8840.888 2.808 0.985 2.995 00 186.4604/27/2010,18:20:470 28.8840.888 2.831 0.985 2.996 00 186.44804/27/2010,18:21:470 28.8840.888 2.899 0.985 2.996 00 186.5604/27/2010,18:22:470 28.8840.888 2.864 0.985 2.998 00 186.34204/27/2010,18:23:470 28.8850.888 3.064 0.985 2.997 00 186.06504/27/2010,18:24:470 28.8860.888 2.733 0.985 2.998 00 185.82404/27/2010,18:25:470 28.8860.888 2.778 0.985 2.997 00 185.65204/27/2010,18:26:470 28.8860.888 2.763 0.985 2.997 00 185.55104/27/2010,18:27:470 28.8860.888 2.811 0.985 2.996 00 185.43504/27/2010,18:28:470 28.8860.888 2.873 0.985 3.001 00 185.30704/27/2010,18:29:470 28.8860.888 2.878 0.985 2.998 00 185.24904/27/2010,18:30:470 28.8860.888 2.902 0.985 2.998 00 185.1304/27/2010,18:31:470 28.8880.888 2.873 0.985 2.996 00 185.29604/27/2010,18:32:480 28.890.888 2.634 0.985 2.997 00 185.37204/27/2010,18:33:480 28.8910.888 2.897 0.985 2.997 00 185.50704/27/2010,18:34:480 28.8920.888 2.9 0.985 2.996 00 185.50904/27/2010,18:35:480 28.8930.888 2.9 0.985 2.995 00 185.50904/27/2010,18:36:480 28.8940.888 2.899 0.985 2.994 00 185.546Time:date,hh:mm:ss04/27/2010,18:02:4604/27/2010,18:03:4604/27/2010,18:04:4604/27/2010,18:05:4604/27/2010,18:06:4604/27/2010,18:07:4604/27/2010,18:08:4704/27/2010,18:09:4704/27/2010,18:10:4704/27/2010,18:11:4704/27/2010,18:12:4704/27/2010,18:13:4704/27/2010,18:14:4704/27/2010,18:15:4704/27/2010,18:16:4704/27/2010,18:17:4704/27/2010,18:18:4704/27/2010,18:19:4704/27/2010,18:20:4704/27/2010,18:21:4704/27/2010,18:22:4704/27/2010,18:23:4704/27/2010,18:24:4704/27/2010,18:25:4704/27/2010,18:26:4704/27/2010,18:27:4704/27/2010,18:28:4704/27/2010,18:29:4704/27/2010,18:30:4704/27/2010,18:31:4704/27/2010,18:32:4804/27/2010,18:33:4804/27/2010,18:34:4804/27/2010,18:35:4804/27/2010,18:36:48Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.503 251.87470.803 70.451500 71.736 76.289274.401 250.5670.851 70.451500 71.734 76.353274.539 250.33370.858 70.451500 71.731 76.388274.514 252.25370.835 70.476500 71.758 76.366274.403 250.22170.921 70.507500 71.816 76.43274.449 251.37170.901 70.507500 71.814 76.389274.456 252.08970.918 70.507500 71.804 76.396274.667 249.85971.011 70.609500 71.873 76.462274.521 252.59370.99 70.619500 71.877 76.342274.525 250.96870.973 70.621500 71.878 76.297274.593 250.5170.98 70.619500 71.868 76.34274.392 252.68870.947 70.659500 71.905 76.389274.618 249.68670.906 70.675500 71.916 76.369274.473 252.26770.913 70.675500 71.909 76.289274.439 251.59870.845 70.672500 71.908 76.34274.61 250.26270.906 70.724500 71.958 76.457274.509 253.21470.859 70.707500 71.95 76.452274.592 250.28770.789 70.694500 71.926 76.424274.543 252.08570.773 70.681500 71.912 76.468274.664 252.38170.775 70.723500 71.956 76.513274.651 250.07470.776 70.728500 71.961 76.494274.485 253.33870.774 70.717500 71.934 76.478274.613 250.44870.727 70.698500 71.913 76.459274.52 251.75170.73 70.68500 71.908 76.379274.514 252.77370.732 70.723500 71.945 76.425274.675 250.13270.677 70.725500 71.923 76.434274.484 253.37170.671 70.695500 71.91 76.438274.65 251.16770.643 70.683500 71.902 76.379274.643 251.57170.6 70.675500 71.875 76.309274.483 253.27170.469 70.667500 71.852 76.158274.658 250.31270.456 70.664500 71.863 76.146274.712 253.22270.496 70.677500 71.865 76.195274.71 252.02570.455 70.674500 71.852 76.203274.665 251.00170.398 70.649500 71.819 76.128274.648 253.68570.35 70.622500 71.757 76.079Time:date,hh:mm:ss04/27/2010,18:02:4604/27/2010,18:03:4604/27/2010,18:04:4604/27/2010,18:05:4604/27/2010,18:06:4604/27/2010,18:07:4604/27/2010,18:08:4704/27/2010,18:09:4704/27/2010,18:10:4704/27/2010,18:11:4704/27/2010,18:12:4704/27/2010,18:13:4704/27/2010,18:14:4704/27/2010,18:15:4704/27/2010,18:16:4704/27/2010,18:17:4704/27/2010,18:18:4704/27/2010,18:19:4704/27/2010,18:20:4704/27/2010,18:21:4704/27/2010,18:22:4704/27/2010,18:23:4704/27/2010,18:24:4704/27/2010,18:25:4704/27/2010,18:26:4704/27/2010,18:27:4704/27/2010,18:28:4704/27/2010,18:29:4704/27/2010,18:30:4704/27/2010,18:31:4704/27/2010,18:32:4804/27/2010,18:33:4804/27/2010,18:34:4804/27/2010,18:35:4804/27/2010,18:36:48Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal77.858 620.494 580.821 642.436 615.58177.877 623.571 583.725 645.635 618.6777.894 626.668 586.662 648.854 621.79377.91 629.797 589.554 652.107 624.86877.928 632.894 592.512 655.326 628.01477.946 635.99 595.391 658.546 631.07677.965 639.076 598.345 661.754 634.21877.981 642.238 601.201 665.041 637.25677.999 645.315 604.16 668.241 640.40378.017 648.4 607.063 671.449 643.4978.032 651.524 609.974 674.697 646.58678.05 654.643 612.913 677.941 649.71378.068 657.713 615.797 681.134 652.78178.086 660.822 618.726 684.366 655.89678.105 663.982 621.623 687.652 658.97778.122 667.07 624.549 690.864 662.08978.139 670.15 627.454 694.066 665.1878.155 673.253 630.378 697.293 668.28978.169 676.391 633.281 700.555 671.37678.184 679.46 636.227 703.746 674.5178.2 682.554 639.108 706.964 677.57478.215 685.706 642.061 710.242 680.71578.228 688.79 644.942 713.448 683.77978.242 691.882 647.889 716.663 686.91378.255 694.977 650.754 719.88 689.9678.267 698.12 653.703 723.149 693.09678.279 701.2 656.604 726.351 696.18178.291 704.304 659.515 729.578 699.27778.297 707.435 662.449 732.833 702.39678.308 710.537 665.338 736.058 705.46878.316 713.63 668.266 739.274 708.58278.327 716.71 671.167 742.476 711.66678.333 719.877 674.094 745.767 714.77878.343 722.956 677.004 748.968 717.87178.351 726.035 679.938 752.168 720.99Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: aux: Stack Flow: Stack Temp:date,hh:mm:ss in-H2O in-Hg l/minin-Hg l/min in-Hg unit fraction degF04/27/2010,18:37:480 28.8950.888 2.925 0.985 2.997 00 185.60104/27/2010,18:38:480 28.8960.888 2.889 0.985 2.996 00 185.67504/27/2010,18:39:480 28.8960.888 2.875 0.985 2.997 00 185.90204/27/2010,18:40:480 28.8970.888 2.883 0.985 2.996 00 186.13504/27/2010,18:41:480 28.8980.888 2.881 0.985 2.995 00 185.58804/27/2010,18:42:480 28.90.888 2.904 0.985 2.998 00 185.74304/27/2010,18:43:480 28.9010.888 2.909 0.985 2.999 00 185.85304/27/2010,18:44:480 28.9020.888 2.906 0.985 3.001 00 185.90804/27/2010,18:45:48 Sampling complete 240.233533 Minutes sampledC:Drive Code:0Compact Flash Code:0Time:date,hh:mm:ss04/27/2010,18:37:4804/27/2010,18:38:4804/27/2010,18:39:4804/27/2010,18:40:4804/27/2010,18:41:4804/27/2010,18:42:4804/27/2010,18:43:4804/27/2010,18:44:4804/27/2010,18:45:48C:Drive Code:0Compact Flash Code:0Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp: AuxTemp:degFdegF degFdegFdegFdegFdegF274.833 250.50770.336 70.619500 71.738 75.941274.703 252.35370.284 70.572500 71.711 75.885274.711 252.09870.133 70.507500 71.688 75.831274.789 250.5470.109 70.501500 71.668 75.792274.664 253.63470.097 70.469500 71.63 75.824274.832 250.41770.097 70.45500 71.623 75.799274.725 252.37970.086 70.439500 71.587 75.696274.747 252.6970.072 70.408500 71.572 75.648Time:date,hh:mm:ss04/27/2010,18:37:4804/27/2010,18:38:4804/27/2010,18:39:4804/27/2010,18:40:4804/27/2010,18:41:4804/27/2010,18:42:4804/27/2010,18:43:4804/27/2010,18:44:4804/27/2010,18:45:48C:Drive Code:0Compact Flash Code:0Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degFliters STP liters STP liters nominal liters nominal78.355 729.158 682.837 755.414 724.07178.361 732.265 685.792 758.642 727.21178.367 735.353 688.672 761.85 730.27178.371 738.431 691.634 765.049 733.41978.373 741.596 694.504 768.336 736.46878.375 744.655 697.458 771.514 739.60678.378 747.741 700.342 774.72 742.6778.379 750.878 703.28 777.977 745.791Hg TESTPARAMETERS 4/27/2010 1:18 PMXducerPitotBarom Flow 1Vac 1 Flow 2 Vac 2 aux LoadGain1.12 3.410.17 1100 0.189 1100 10Offset0.001 17.40.004 0.5 0.004 0.5 00TstdPstdGam 1 Gam 2CPL 2 CPL 16829.92 1.00130.9812 526.106 526.211Prop timeProbe min Filter min Stack min Test time0.5225 250150 240LpmMotor V Log Time File Suffix Load Proportion0.82.6 60 South 4-27-10 r3 Pitot ManualTime:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: Leak 1: Stack Flow:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg cc per M cc per M04/27/2010,13:18:390 28.8050.149 11.149 0.095 11.258 2.534 5.06904/27/2010,13:18:540 28.8050.118 11.679 0.085 11.312 350.737 363.41204/27/2010,13:19:090 28.8050.1 11.898 0.08 11.35 363.406 371.01504/27/2010,13:19:250 28.8060.094 11.862 0.065 11.377 40.541 40.54904/27/2010,13:19:400 28.8060.093 11.661 0.063 11.386 30.406 12.67204/27/2010,13:19:550 28.8060.094 11.661 0.062 11.405 22.805 2.53404/27/2010,13:20:100 28.8060.09 11.478 0.066 11.42 17.737 2.53404/27/2010,13:20:250 28.8050.088 12.173 0.058 11.432 17.737 22.80904/27/2010,13:20:410 28.8070.086 12.022 0.059 11.438 15.203 27.87804/27/2010,13:20:560 28.8070.085 11.91 0.056 11.436 12.669 27.87804/27/2010,13:21:110 28.8070.084 12.607 0.058 11.447 7.602 10.13704/27/2010,13:21:260 28.8080.084 12.052 0.054 11.454 5.068 7.60304/27/2010,13:21:420 28.810.084 12.228 0.055 11.457 2.534 7.60304/27/2010,13:21:570 28.8090.083 11.632 0.055 11.458 5.068 5.06904/27/2010,13:22:120 28.8090.082 11.79 0.056 11.459 2.534 5.06904/27/2010,13:22:270 28.8090.082 11.875 0.058 11.466 5.068 2.53404/27/2010,13:22:420 28.8090.083 12.166 0.053 11.464 2.534 5.06904/27/2010,13:22:54 Sampling terminated byoperator 4.314483 Minutes sampledC:Drive Code:0Compact Flash Code:0Hg TESTPARAMETERS 4/27/2010 6:49 PMHg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,13:18:3904/27/2010,13:18:5404/27/2010,13:19:0904/27/2010,13:19:2504/27/2010,13:19:4004/27/2010,13:19:5504/27/2010,13:20:1004/27/2010,13:20:2504/27/2010,13:20:4104/27/2010,13:20:5604/27/2010,13:21:1104/27/2010,13:21:2604/27/2010,13:21:4204/27/2010,13:21:5704/27/2010,13:22:1204/27/2010,13:22:2704/27/2010,13:22:4204/27/2010,13:22:54C:Drive Code:0Compact Flash Code:0Hg TESTStack Temp: Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp:degF degFdegF degFdegFdegFdegF78.995 275.189 255.44468.959 70.071500 71.7478.418 275.105 253.34468.891 70.059500 71.7477.762 275.073 250.60968.903 70.059500 71.79977.924 275.037 250.12768.98 70.059500 71.82377.839 275.055 252.48668.995 70.059500 71.84676.684 275.077 255.16468.995 70.059500 71.85275.951 275.101 255.62168.89 70.059500 71.8675.131 275.133 253.59168.826 70.056500 71.89274.472 275.109 250.60968.806 70.059500 71.90874.123 275.043 249.56768.773 70.049500 71.89873.769 274.831 251.40468.714 69.996500 71.85273.647 274.695 254.30168.703 69.994500 71.8773.54 274.545 255.37568.629 69.988500 71.88273.484 274.461 253.82768.546 69.982500 71.89973.574 274.477 250.87668.555 69.974500 71.90873.639 274.537 249.44468.546 69.952500 71.90873.507 274.629 250.54768.546 69.953500 71.914Hg TESTXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,13:18:3904/27/2010,13:18:5404/27/2010,13:19:0904/27/2010,13:19:2504/27/2010,13:19:4004/27/2010,13:19:5504/27/2010,13:20:1004/27/2010,13:20:2504/27/2010,13:20:4104/27/2010,13:20:5604/27/2010,13:21:1104/27/2010,13:21:2604/27/2010,13:21:4204/27/2010,13:21:5704/27/2010,13:22:1204/27/2010,13:22:2704/27/2010,13:22:4204/27/2010,13:22:54C:Drive Code:0Compact Flash Code:0Hg TESTAuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degF degFliters STP liters STP liters nominal liters nominal75.65379.22 0.011 0.02 0.011 0.02175.61579.22 0.022 0.027 0.023 0.02975.7279.217 0.029 0.029 0.03 0.0375.72379.216 0.033 0.029 0.034 0.0375.75179.214 0.038 0.029 0.04 0.0375.74379.211 0.042 0.03 0.044 0.03275.72979.207 0.046 0.045 0.048 0.04875.64879.204 0.049 0.048 0.051 0.05175.63979.201 0.051 0.05 0.053 0.05375.62879.2 0.051 0.052 0.053 0.05575.57179.197 0.053 0.053 0.055 0.05775.59779.193 0.053 0.055 0.055 0.05975.59779.19 0.055 0.055 0.057 0.05975.60279.187 0.055 0.057 0.057 0.06175.58679.184 0.057 0.057 0.059 0.06175.55679.183 0.057 0.059 0.059 0.06375.5579.181 0.057 0.059 0.059 0.063Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: Leak 1: Stack Flow:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg cc per M cc per MXducerPitotBarom Flow 1Vac 1 Flow 2 Vac 2 aux LoadGain1.12 3.410.17 1100 0.189 1100 10Offset0.001 17.40.004 0.5 0.004 0.5 00TstdPstdGam 1 Gam 2CPL 2 CPL 16829.92 1.00130.9812 526.106 526.211Prop timeProbe min Filter min Stack min Test time0.5225 250150 240LpmMotor V Log Time File Suffix Load Proportion0.82.6 60 South 4-27-10 r3 Pitot ManualTime:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: Leak 1: Stack Flow:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg cc per M cc per M04/27/2010,18:49:210 28.9060.824 6.71 0.887 6.603 2.534 2.53404/27/2010,18:49:370 28.9060.885 8.986 0.956 8.69 956.324 847.47204/27/2010,18:49:520 28.9060.681 10.251 0.648 9.865 1321.197 1273.24104/27/2010,18:50:070 28.9060.418 10.982 0.376 10.499 1266.919 1127.78304/27/2010,18:50:220 28.9060.301 11.338 0.255 10.878 815.896 740.02804/27/2010,18:50:370 28.9060.231 12.09 0.172 11.108 552.377 370.01404/27/2010,18:50:530 28.9060.161 11.677 0.122 11.239 344.602 255.96904/27/2010,18:51:080 28.9060.116 12.155 0.098 11.315 215.376 182.47304/27/2010,18:51:230 28.9060.099 11.719 0.076 11.357 129.226 149.52604/27/2010,18:51:380 28.9070.092 11.823 0.067 11.377 58.278 88.70204/27/2010,18:51:540 28.9070.089 12.076 0.061 11.396 15.203 48.15304/27/2010,18:52:090 28.9070.087 11.919 0.057 11.409 0 30.41204/27/2010,18:52:240 28.9070.085 11.87 0.053 11.418 0 20.27504/27/2010,18:52:390 28.9070.085 11.981 0.054 11.428 0 12.67204/27/2010,18:52:540 28.9070.086 12.079 0.053 11.427 0 7.60304/27/2010,18:53:100 28.9080.084 11.835 0.049 11.428 0 7.60304/27/2010,18:53:250 28.9080.085 12.376 0.052 11.442 2.534 5.06904/27/2010,18:53:400 28.9080.085 11.838 0.054 11.444 2.534 5.06904/27/2010,18:53:550 28.9090.084 11.868 0.057 11.453 2.534 5.06904/27/2010,18:54:100 28.9090.085 11.918 0.053 11.464 0 5.06904/27/2010,18:54:260 28.9090.084 11.908 0.053 11.46 12.669 5.06904/27/2010,18:54:410 28.910.084 12.292 0.054 11.461 15.203 2.534Time:date,hh:mm:ssXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,18:49:2104/27/2010,18:49:3704/27/2010,18:49:5204/27/2010,18:50:0704/27/2010,18:50:2204/27/2010,18:50:3704/27/2010,18:50:5304/27/2010,18:51:0804/27/2010,18:51:2304/27/2010,18:51:3804/27/2010,18:51:5404/27/2010,18:52:0904/27/2010,18:52:2404/27/2010,18:52:3904/27/2010,18:52:5404/27/2010,18:53:1004/27/2010,18:53:2504/27/2010,18:53:4004/27/2010,18:53:5504/27/2010,18:54:1004/27/2010,18:54:2604/27/2010,18:54:41Stack Temp: Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp:degF degFdegF degFdegFdegFdegFStack Temp: Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp:degF degFdegF degFdegFdegFdegF135.865 273.131 249.84769.941 70.339500 71.439132.17 272.921 249.18369.929 70.339500 71.457129.215 273.064 251.77569.923 70.336500 71.501126.99 273.43 255.47869.947 70.335500 71.516125.042 274.01 256.92969.923 70.328500 71.52123.408 274.67 255.52769.921 70.339500 71.525122.063 275.238 252.30269.932 70.323500 71.54120.974 275.658 249.75769.879 70.313500 71.56119.996 275.85 250.48469.885 70.313500 71.568119.172 275.835 253.74569.867 70.307500 71.572118.246 275.698 256.09169.856 70.302500 71.575117.264 275.543 255.66869.844 70.291500 71.582116.13 275.396 253.04269.879 70.297500 71.609115.301 275.32 250.2369.859 70.283500 71.619114.962 275.294 250.14969.847 70.283500 71.628114.773 275.288 252.96769.835 70.283500 71.628114.654 275.403 255.61469.847 70.283500 71.628114.732 275.614 255.65369.841 70.283500 71.638114.719 275.82 253.32569.835 70.283500 71.674114.403 276.024 250.32569.835 70.283500 71.684114.359 276.134 249.73569.835 70.274500 71.684114.418 276.142 252.32569.835 70.283500 71.684Time:date,hh:mm:ssXducerGainOffsetTstd68Prop time0.5Lpm0.8Time:date,hh:mm:ss04/27/2010,18:49:2104/27/2010,18:49:3704/27/2010,18:49:5204/27/2010,18:50:0704/27/2010,18:50:2204/27/2010,18:50:3704/27/2010,18:50:5304/27/2010,18:51:0804/27/2010,18:51:2304/27/2010,18:51:3804/27/2010,18:51:5404/27/2010,18:52:0904/27/2010,18:52:2404/27/2010,18:52:3904/27/2010,18:52:5404/27/2010,18:53:1004/27/2010,18:53:2504/27/2010,18:53:4004/27/2010,18:53:5504/27/2010,18:54:1004/27/2010,18:54:2604/27/2010,18:54:41AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degF degFliters STP liters STP liters nominal liters nominalAuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degF degF liters STP liters STP liters nominal liters nominal75.5178.375 0.45 0.362 0.467 0.38475.49978.374 0.714 0.664 0.741 0.70575.50778.374 0.915 0.797 0.95 0.84675.5378.374 1.04 0.884 1.079 0.93975.54378.373 1.113 0.925 1.155 0.98375.5378.371 1.164 0.977 1.209 1.03875.54678.371 1.195 1.013 1.241 1.07675.54678.371 1.206 1.031 1.252 1.09575.5578.371 1.206 1.04 1.252 1.10475.54178.371 1.206 1.047 1.252 1.11275.55578.371 1.206 1.053 1.252 1.11875.5578.371 1.206 1.054 1.252 1.1275.5378.37 1.206 1.056 1.252 1.12175.4978.368 1.206 1.058 1.252 1.12375.48278.368 1.206 1.06 1.252 1.12575.4978.367 1.208 1.06 1.254 1.12575.5178.367 1.208 1.061 1.254 1.12775.5478.367 1.208 1.063 1.254 1.12975.49478.367 1.208 1.063 1.254 1.12975.4678.365 1.217 1.065 1.264 1.13175.42678.363 1.219 1.065 1.266 1.13175.43478.364 1.219 1.067 1.266 1.133Time:Pitot:Barometric: Flowmeter1: Vaccuum1: Flowmeter2: Vacuum2: Leak 1: Stack Flow:date,hh:mm:ssin-H2O in-Hg l/minin-Hg l/min in-Hg cc per M cc per M04/27/2010,18:54:560 28.910.084 11.971 0.057 11.469 15.203 5.06904/27/2010,18:55:110 28.910.085 11.668 0.05 11.464 5.068 2.53404/27/2010,18:55:260 28.910.083 12.068 0.045 11.461 2.534 2.53404/27/2010,18:55:35 Sampling terminated byoperator 6.239567 Minutes sampledC:Drive Code:0Compact Flash Code:0Time:date,hh:mm:ss04/27/2010,18:54:5604/27/2010,18:55:1104/27/2010,18:55:2604/27/2010,18:55:35C:Drive Code:0Compact Flash Code:0Stack Temp: Sorbent Temp: Probe Temp: Box Internal Temp: DGM#1 Temp: Condenser#1 Temp: DGM#2 Temp:degF degFdegF degFdegFdegFdegF114.535 276.114 255.30569.835 70.274500 71.684114.53 276.052 255.78869.835 70.274500 71.691114.604 276.03 254.44269.835 70.26250071.7Time:date,hh:mm:ss04/27/2010,18:54:5604/27/2010,18:55:1104/27/2010,18:55:2604/27/2010,18:55:35C:Drive Code:0Compact Flash Code:0AuxTemp: Cold Juntion Temp: DGM1*: DGM2*: DGM1: DGM2:degF degFliters STP liters STP liters nominal liters nominal75.44378.363 1.221 1.067 1.268 1.13375.46978.363 1.221 1.067 1.268 1.13375.49178.363 1.223 1.067 1.269 1.133

# L2010-275 

# APPENDIX A.6

CEMS DATA

# Calibration Error Test at Run 1 . STRATA Version 3.2

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 9:09:16 0.076 0.019 0.028 0.86 9.957 11.823

4/28/2010 9:10:16 3.192 2.633 -0.153 -0.17 0.871 6.301

4/28/2010 9:11:14 22.014 17.799 -0.097 -0.17 0.756 0.003

4/28/2010 9:12:14 10.73 10.513 -0.047 -0.15 0.73 0.003

4/28/2010 9:13:14 3.607 3.469 41.837 -0.15 0.726 0.003

4/28/2010 9:14:14 0.09 0.068 74.619 -0.15 0.725 0.002

4/28/2010 9:15:14 0.049 0.026 44.775 -0.14 0.734 0.003

4/28/2010 9:16:14 12.48 0.051 25.45 66.89 0.749 0.003

4/28/2010 9:17:14 20.907 0.019 -0.038 198.49 0.695 0.002

4/28/2010 9:18:14 20.776 0.065 -0.05 173.23 0.723 0.003

4/28/2010 9:19:14 20.905 0.019 -0.184 95.62 0.726 0.002

4/28/2010 9:20:14 11.749 4.889 5.399 68.8 0.726 0.003

4/28/2010 9:21:14 0.172 0.109 3.434 10.32 0.581 0.003

4/28/2010 9:22:14 0.164 0.14 1.658 3.18 0.359 0.002

4/28/2010 9:23:14 18.833 0.088 1.449 3.06 1.151 0.004

4/28/2010 9:24:14 20.722 0.072 1.368 2.67 24.782 6.589

4/28/2010 9:25:14 20.737 0.068 1.273 2.65 24.86 24.706

4/28/2010 9:26:14 20.75 0.068 1.363 2.65 24.952 24.79

4/28/2010 9:27:14 20.748 0.068 1.269 2.66 24.977 24.844

4/28/2010 9:28:14 20.729 0.068 1.156 2.65 21.106 24.913

4/28/2010 9:29:14 20.733 0.073 1.203 2.43 12.1 17.986

4/28/2010 9:30:14 20.39 0.295 1.153 2.61 12.047 11.88

4/28/2010 9:31:14 20.748 0.084 1.089 2.61 7.423 11.007

Calibration Error Test at Run 1

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Low-range Mid-range High-range

O2 CC281576 SG9135786 CC285394

CO2 CC281576 SG9135786 CC285394

SO2 CC281576 CC308434 CC122146

CO CC281576 CC91533 CC41590

CH4 CC281576 CC178755 CC245119 CC155902

NMHC CC281576 CC178755 CC245119 CC155902

Date/Time 4/28/2010 9:31:30 PASSED

Analyte O2 CO2 SO2 CO CH4 NMHC

Units % % ppm ppm ppm ppm

Zero Ref Cyl 0 0 0000

Zero Avg 0.061 0.019 -0.194 -0.17 0.364 0.003

Zero Error% 0.3 0.1 0.2 0.1 1.4 0

Low Ref Cyl 7.049 7.001

Low Avg 7.093 6.836

Low Error% 0.2 0.7

Mid Ref Cyl 9.993 10 45.2 90.16 12.05 12.03

Mid Avg 9.959 10.206 44.566 92.41 12.108 11.901

Mid Error% 0.2 1.2 0.7 1.1 0.2 0.5

High Ref Cyl 22 17.76 91.01 201 25.37 24.86

High Avg 22.027 17.808 90.231 202.5 24.992 24.85

High Error% 0.1 0.3 0.9 0.7 1.5 0

# Initial System Bias Check for Run 1 . STRATA Version 3.2

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 9:32:32 12.309 0.087 1.144 2.39 7.093 6.819

4/28/2010 9:33:32 0.196 0.086 1.1 2.64 1.653 6.157

4/28/2010 9:34:32 0.157 0.084 1.099 2.65 0.48 0.574

4/28/2010 9:35:32 0.145 0.079 1.154 2.66 0.336 0.042

4/28/2010 9:36:32 6.344 6.514 1.138 2.61 0.336 0.004

4/28/2010 9:37:32 9.873 10.135 1.255 2.14 0.336 0.003

4/28/2010 9:38:33 7.756 7.856 1.727 2.08 0.339 0.004

4/28/2010 9:39:33 0.17 0.158 28.144 2.37 0.336 0.004

4/28/2010 9:40:33 0.148 0.115 38.025 2.54 0.336 0.004

4/28/2010 9:41:33 0.141 0.112 40.37 2.38 0.336 0.003

4/28/2010 9:42:33 0.244 0.3 41.279 2.38 0.336 0.003

4/28/2010 9:43:33 17.748 0.928 26.649 117.09 0.336 0.007

4/28/2010 9:44:33 20.664 0.105 3.785 204.78 0.337 0.018

Initial System Bias Check for Run 1

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

CO CC281576 CC41590

CH4 CC281576 CC178755

NMHC CC281576 CC178755

Date/Time 4/28/2010 9:45:13 PASSED

Analyte O2 CO2 SO2 CO CH4 NMHC

Units % % ppm ppm ppm ppm

Zero Ref Cyl 000000

Zero Cal 0.061 0.019 -0.194 -0.17 0.364 0.003

Zero Avg 0.146 0.08 1.094 2.68 0.336 0.004

Zero Bias% 0.4 0.3 1.4 1.4 0.1 0

Zero Drift%

Span Ref Cyl 9.993 10 45.2 201 7.049 7.001

Span Cal 9.959 10.206 44.566 202.5 7.093 6.836

Span Avg 9.882 10.155 41.06 206.13 7.094 6.837

Span Bias% 0.4 0.3 3.9 1.8 0 0

Span Drift%

# Test Run 1 Begin. STRATA Version 3.2

Operator: M. Martin

Plant Nam e Dominion Southampton

Location: Common Stack

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 9:46:13 13.618 6.638 5.001 160.43 0.336 0.003

4/28/2010 9:47:13 6.663 12.641 14.208 38.39 0.432 0.003

Begin calculating run averages

4/28/2010 9:49:05 6.827 12.516 16.121 36.79 0.576 0.005

4/28/2010 9:50:05 6.854 12.509 12.531 31.71 0.576 0.003

4/28/2010 9:51:05 6.584 12.718 9.937 35.65 0.576 0.003

4/28/2010 9:52:06 6.498 12.775 11.247 41.67 0.576 0.003

4/28/2010 9:53:06 6.633 12.672 11.059 39.07 0.576 0.003

4/28/2010 9:54:06 6.632 12.694 10.679 33.38 0.576 0.003

4/28/2010 9:55:06 6.594 12.727 10.889 36.22 0.576 0.003

4/28/2010 9:56:06 6.589 12.741 11.049 35.45 0.576 0.003

4/28/2010 9:57:06 6.665 12.66 10.254 37.85 0.576 0.003

4/28/2010 9:58:06 6.675 12.643 13.9 36.56 0.576 0.003

4/28/2010 9:59:06 6.589 12.716 13.2 49.08 0.576 0.003

4/28/2010 10:00:06 6.677 12.66 12.085 54.34 0.576 0.003

4/28/2010 10:01:06 6.678 12.646 12.094 49.98 0.576 0.003

4/28/2010 10:02:06 6.465 12.825 12.609 61.17 0.576 0.003

4/28/2010 10:03:06 6.564 12.75 11.834 71.54 0.576 0.003

4/28/2010 10:04:06 6.824 12.543 12.691 45.11 0.576 0.003

4/28/2010 10:05:06 6.685 12.652 11.359 34.52 0.576 0.003

4/28/2010 10:06:06 6.569 12.739 11.599 35.03 0.576 0.003

4/28/2010 10:07:06 6.455 12.834 10.606 41.63 0.576 0.004

4/28/2010 10:08:06 6.508 12.787 10.752 48.04 0.576 0.003

4/28/2010 10:09:06 6.723 12.61 11.263 52.2 0.576 0.003

4/28/2010 10:10:06 6.664 12.656 11.348 43.77 0.576 0.003

4/28/2010 10:11:06 6.486 12.792 11.113 44.19 0.576 0.003

4/28/2010 10:12:06 6.57 12.722 9.63 43.89 0.576 0.003

4/28/2010 10:13:06 6.572 12.723 9.015 48.4 0.576 0.003

4/28/2010 10:14:06 6.568 12.712 8.358 67.37 0.586 0.003

4/28/2010 10:15:06 6.458 12.803 8.141 105.62 0.636 0.003

4/28/2010 10:16:07 6.492 12.785 7.608 86.19 0.756 0.003

4/28/2010 10:17:07 6.543 12.753 7.649 58.25 0.635 0.003

4/28/2010 10:18:07 6.494 12.78 7.684 68.62 0.587 0.003

4/28/2010 10:19:07 6.528 12.745 13.626 85.38 0.589 0.003

4/28/2010 10:20:07 6.548 12.75 11.979 69.91 0.597 0.003

4/28/2010 10:21:07 6.54 12.752 11.068 74.39 0.579 0.003

4/28/2010 10:22:07 6.496 12.78 10.657 106.01 0.605 0.003

4/28/2010 10:23:07 6.537 12.74 10.843 93.38 0.662 0.004

4/28/2010 10:24:07 6.64 12.659 11.958 88.67 0.622 0.003

4/28/2010 10:25:07 6.661 12.636 12.211 66.17 0.605 0.003

4/28/2010 10:26:07 6.585 12.701 11.32 58.44 0.594 0.003

4/28/2010 10:27:07 6.434 12.828 11.187 58.86 0.576 0.003

4/28/2010 10:28:07 6.405 12.849 11.012 55.02 0.576 0.003

4/28/2010 10:29:07 6.595 12.708 11.086 45.28 0.576 0.003

4/28/2010 10:30:07 6.55 12.736 10.825 39.14 0.575 0.004

4/28/2010 10:31:07 6.433 12.837 9.622 44.6 0.595 0.003

# 4/28/2010 10:32:07 6.574 12.703 13.839 46.15 0.59 0.004

4/28/2010 10:33:07 6.556 12.738 12.592 40.53 0.576 0.003

4/28/2010 10:34:07 6.443 12.829 12.503 41.03 0.576 0.003

4/28/2010 10:35:07 6.438 12.835 12.55 43.9 0.576 0.003

4/28/2010 10:36:07 6.479 12.802 12.126 43.49 0.576 0.004

4/28/2010 10:37:07 6.483 12.811 12.521 41.91 0.598 0.003

4/28/2010 10:38:07 6.308 12.965 12.6 46.19 0.588 0.003

4/28/2010 10:39:07 6.457 12.851 10.348 47.28 0.576 0.003

4/28/2010 10:40:07 6.619 12.712 11.682 35.48 0.576 0.003

4/28/2010 10:41:07 6.49 12.804 11.793 34.49 0.576 0.003

4/28/2010 10:42:07 6.499 12.806 11.093 32.64 0.576 0.003

4/28/2010 10:43:07 6.494 12.796 11.067 35.22 0.576 0.003

4/28/2010 10:44:07 6.454 12.821 9.918 41.74 0.576 0.003

4/28/2010 10:45:07 6.494 12.782 11.211 35.25 0.576 0.003

4/28/2010 10:46:07 6.371 12.899 11.607 31.66 0.576 0.004

4/28/2010 10:47:07 6.376 12.884 11.815 32.85 0.576 0.004

4/28/2010 10:48:07 6.515 12.763 11.621 30.29 0.576 0.003

4/28/2010 10:49:07 6.42 12.856 11.375 28.45 0.576 0.004

4/28/2010 10:50:07 6.487 12.778 11.274 29.61 0.576 0.004

4/28/2010 10:51:07 6.406 12.859 12.332 33.86 0.575 0.004

4/28/2010 10:52:07 6.448 12.847 10.803 32.44 0.576 0.004

4/28/2010 10:53:07 6.602 12.705 9.124 27.08 0.576 0.003

4/28/2010 10:54:07 6.404 12.874 9.29 26.41 0.576 0.003

4/28/2010 10:55:07 6.306 12.937 10.062 27.85 0.576 0.004

4/28/2010 10:56:07 6.514 12.797 9.79 27.85 0.575 0.004

4/28/2010 10:57:07 6.372 12.91 10.154 26.53 0.575 0.003

4/28/2010 10:58:07 6.313 12.948 12.327 28.99 0.575 0.004

4/28/2010 10:59:07 6.434 12.867 12.265 28.04 0.576 0.004

4/28/2010 11:00:07 6.548 12.771 10.561 26.3 0.582 0.004

4/28/2010 11:01:07 6.439 12.849 14.766 28.31 0.605 0.003

4/28/2010 11:02:07 6.487 12.825 14.101 29.35 0.605 0.004

4/28/2010 11:03:07 6.59 12.739 11.909 25.77 0.605 0.003

4/28/2010 11:04:07 6.402 12.881 11.117 26.31 0.586 0.003

4/28/2010 11:05:07 6.446 12.844 9.781 27.37 0.576 0.004

4/28/2010 11:06:05 6.365 12.903 9.357 28.41 0.576 0.003

4/28/2010 11:07:05 6.448 12.859 8.623 28.62 0.579 0.003

4/28/2010 11:08:05 6.532 12.779 8.255 26.54 0.605 0.003

4/28/2010 11:09:06 6.414 12.874 9.917 25.97 0.578 0.003

4/28/2010 11:10:06 6.315 12.962 10.684 27.34 0.576 0.004

4/28/2010 11:11:06 6.447 12.843 10.014 26.35 0.576 0.003

4/28/2010 11:12:06 6.614 12.721 11.828 28.19 0.576 0.003

4/28/2010 11:13:06 6.356 12.922 12.159 26.57 0.576 0.003

4/28/2010 11:14:06 6.348 12.919 13.389 28.75 0.576 0.003

4/28/2010 11:15:06 6.539 12.795 13.963 29.29 0.576 0.003

4/28/2010 11:16:06 6.55 12.766 12.76 26.64 0.576 0.003

4/28/2010 11:17:06 6.432 12.87 12.132 27.38 0.576 0.003

4/28/2010 11:18:06 6.495 12.817 11.718 26.91 0.576 0.003

4/28/2010 11:19:06 6.546 12.766 10.686 27.02 0.576 0.003

4/28/2010 11:20:06 6.453 12.843 9.897 26.54 0.576 0.003

4/28/2010 11:21:06 6.348 12.929 11.114 27.2 0.576 0.003

4/28/2010 11:22:06 6.539 12.785 14.046 27.87 0.576 0.003

4/28/2010 11:23:06 6.691 12.672 13.773 26.63 0.576 0.003

# 4/28/2010 11:24:06 6.441 12.863 13.284 25.87 0.576 0.003

4/28/2010 11:25:06 6.442 12.862 13.842 25.44 0.576 0.003

4/28/2010 11:26:06 6.495 12.832 14.39 25.23 0.583 0.003

4/28/2010 11:27:06 6.551 12.782 14.098 25.55 0.603 0.003

4/28/2010 11:28:06 6.621 12.698 18.256 25.61 0.576 0.003

4/28/2010 11:29:06 6.443 12.849 14.665 25.85 0.601 0.003

4/28/2010 11:30:06 6.576 12.734 14.234 25.9 0.585 0.004

4/28/2010 11:31:06 6.518 12.78 14.738 25.86 0.591 0.003

4/28/2010 11:32:06 6.533 12.771 15.194 26.09 0.605 0.003

4/28/2010 11:33:06 6.433 12.842 16.086 26.16 0.605 0.004

4/28/2010 11:34:06 6.401 12.864 15.504 26.74 0.605 0.003

4/28/2010 11:35:06 6.558 12.723 14.689 26.23 0.605 0.003

4/28/2010 11:36:06 6.543 12.722 15.349 25.43 0.582 0.003

4/28/2010 11:37:06 6.431 12.811 15.949 25.87 0.594 0.003

4/28/2010 11:38:06 6.507 12.76 15.047 26.51 0.605 0.003

4/28/2010 11:39:06 6.501 12.758 14.354 26.26 0.596 0.003

4/28/2010 11:40:06 6.546 12.711 15.201 26.61 0.579 0.003

4/28/2010 11:41:06 6.448 12.805 13.638 27 0.605 0.003

4/28/2010 11:42:06 6.493 12.766 12.83 27.29 0.605 0.003

4/28/2010 11:43:06 6.489 12.75 15.293 27.68 0.605 0.003

4/28/2010 11:44:06 6.582 12.685 15.614 29.57 0.605 0.003

4/28/2010 11:45:06 6.611 12.671 15.108 27.5 0.605 0.004

4/28/2010 11:46:06 6.522 12.728 15.982 27.39 0.606 0.003

4/28/2010 11:47:07 6.484 12.758 15.248 26.98 0.605 0.003

4/28/2010 11:48:07 6.451 12.784 15.59 26.82 0.605 0.004

Average of Test Run O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 11:48:07 6.515 12.777 12.052 38.77 0.586 0.003

Test Run 1 End

# Final System Bias Check for Run 1 . STRATA Version 3.2

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 11:49:09 7.177 12.258 13.336 29.44 0.606 0.003

4/28/2010 11:50:09 19.136 0.745 5.633 68.87 0.627 0.003

4/28/2010 11:51:09 20.712 0.126 1.522 4.62 3.984 0.004

4/28/2010 11:52:09 20.731 0.112 0.83 3.06 6.933 5.035

4/28/2010 11:53:09 20.735 0.102 0.59 2.93 6.973 6.603

4/28/2010 11:54:09 3.741 0.094 0.558 3.09 6.973 6.627

4/28/2010 11:55:09 0.174 0.091 0.305 3.01 0.395 5.302

4/28/2010 11:56:09 4.467 4.492 0.317 2.92 0.371 0.003

4/28/2010 11:57:09 9.874 10.129 0.371 2.47 0.365 0.004

4/28/2010 11:58:09 7.369 7.45 1.073 2.36 0.352 0.003

4/28/2010 11:59:09 0.172 0.155 27.677 2.64 0.336 0.003

4/28/2010 12:00:09 0.151 0.108 36.819 2.74 0.336 0.004

4/28/2010 12:01:09 0.145 0.096 38.915 2.65 0.336 0.003

4/28/2010 12:02:09 0.144 0.088 39.66 2.66 0.336 0.003

4/28/2010 12:03:09 0.141 0.087 40.269 2.66 0.336 0.003

4/28/2010 12:04:09 17.455 0.094 20.977 119.13 0.336 0.003

Final System Bias Check for Run 1

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

CO CC281576 CC41590

CH4 CC281576 CC178755

NMHC CC281576 CC178755

Date/Time 4/28/2010 12:04:47 PASSED

Analyte O2 CO2 SO2 CO CH4 NMHC

Units % % ppm ppm ppm ppm

Zero Ref Cyl 000000

Zero Cal 0.061 0.019 -0.194 -0.17 0.364 0.003

Zero Avg 0.16 0.091 0.283 2.91 0.395 0.003

Zero Bias% 0.5 0.4 0.5 1.5 0.1 0

Zero Drift% 0.1 0.1 -0.9 0.1 0.2 0

Span Ref Cyl 9.993 10 45.2 201 7.049 7.001

Span Cal 9.959 10.206 44.566 202.5 7.093 6.836

Span Avg 9.88 10.153 40.38 207.21 6.973 6.626

Span Bias% 0.4 0.3 4.6 2.3 0.5 0.8

Span Drift% 0 0 -0.7 0.5 -0.5 -0.8

Ini Zero Avg 0.146 0.08 1.094 2.68 0.336 0.004

Ini Span Avg 9.882 10.155 41.06 206.13 7.094 6.837

Run Avg 6.515 12.777 12.052 38.77 0.586 0.003

Co 0.153 0.085 0.689 2.79 0.366 0.003

Cm 9.881 10.154 40.72 206.67 7.033 6.732

Correct Avg 6.535 12.605 12.83 35.47 0.234 0

# Test Run 2 Begin. STRATA Version 3.2

Operator: M. Martin

Plant Nam e Dominion Southampton

Location: Common Stack

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 12:05:48 13.737 6.475 9.504 162.24 0.336 0.003

4/28/2010 12:06:48 6.479 12.743 17.4 31.74 0.536 0.003

4/28/2010 12:07:48 6.476 12.759 14.363 25.5 0.576 0.003

4/28/2010 12:08:48 6.613 12.643 18.947 25.38 0.576 0.003

4/28/2010 12:09:48 6.554 12.706 18.242 25.4 0.576 0.003

4/28/2010 12:10:48 6.497 12.755 17.427 25.4 0.576 0.003

4/28/2010 12:11:48 6.535 12.735 17.762 25.89 0.576 0.004

4/28/2010 12:12:49 6.584 12.705 17.756 25.93 0.576 0.004

4/28/2010 12:13:49 6.553 12.726 17.535 26.26 0.576 0.003

4/28/2010 12:14:49 6.596 12.686 20.238 27.46 0.593 0.003

4/28/2010 12:15:49 6.63 12.665 20.969 30.26 0.592 0.003

4/28/2010 12:16:49 6.682 12.63 19.617 29.94 0.576 0.003

4/28/2010 12:17:49 6.609 12.682 17.08 27.55 0.576 0.003

4/28/2010 12:18:49 6.494 12.786 16.361 27.66 0.576 0.004

4/28/2010 12:19:49 6.576 12.729 16.55 28.27 0.576 0.003

4/28/2010 12:20:49 6.672 12.647 18.08 29.32 0.576 0.003

4/28/2010 12:21:49 6.553 12.74 17.43 31.14 0.576 0.003

4/28/2010 12:22:49 6.545 12.732 17.342 35.99 0.576 0.004

4/28/2010 12:23:49 6.436 12.831 18.352 35.49 0.576 0.004

4/28/2010 12:24:49 6.641 12.666 17.789 32.84 0.576 0.003

4/28/2010 12:25:49 6.597 12.7 20.099 32.68 0.576 0.004

4/28/2010 12:26:49 6.435 12.836 19.926 36.38 0.576 0.004

4/28/2010 12:27:49 6.51 12.759 19.092 46.73 0.576 0.004

4/28/2010 12:28:49 6.612 12.694 17.795 46.8 0.576 0.004

4/28/2010 12:29:49 6.567 12.72 16.546 41.13 0.576 0.004

4/28/2010 12:30:49 6.601 12.675 16.852 41.74 0.576 0.004

4/28/2010 12:31:49 6.499 12.769 15.922 74.33 0.576 0.004

4/28/2010 12:32:49 6.51 12.76 16.523 71.52 0.576 0.004

4/28/2010 12:33:50 6.588 12.712 16.72 51.78 0.576 0.004

4/28/2010 12:34:50 6.42 12.839 18.741 52.98 0.576 0.004

4/28/2010 12:35:50 6.499 12.774 20.591 52.09 0.576 0.004

4/28/2010 12:36:50 6.575 12.712 21.2 50.1 0.576 0.004

4/28/2010 12:37:50 6.569 12.705 20.759 66.09 0.576 0.004

4/28/2010 12:38:50 6.553 12.712 21.447 53.4 0.576 0.004

4/28/2010 12:39:50 6.565 12.697 21.955 49.27 0.576 0.004

4/28/2010 12:40:48 6.485 12.755 19.404 43.87 0.576 0.004

4/28/2010 12:41:48 6.449 12.784 18.135 42.48 0.576 0.004

4/28/2010 12:42:48 6.49 12.75 17.204 49.79 0.576 0.003

4/28/2010 12:43:48 6.512 12.739 18.546 44.97 0.576 0.004

4/28/2010 12:44:48 6.467 12.781 18.553 46.88 0.576 0.004

4/28/2010 12:45:48 6.514 12.727 16.391 61.6 0.576 0.004

4/28/2010 12:46:48 6.441 12.786 20.929 71.67 0.598 0.004

4/28/2010 12:47:48 6.394 12.831 20.758 95.77 0.606 0.004

4/28/2010 12:48:48 6.488 12.751 19.947 94.02 0.605 0.004

4/28/2010 12:49:48 6.509 12.733 23.184 100.9 0.605 0.004

4/28/2010 12:50:48 6.401 12.826 20.881 100.02 0.604 0.004

# 4/28/2010 12:51:48 6.403 12.82 21.265 132.47 0.576 0.007

Begin calculating run averages

4/28/2010 12:53:12 6.451 12.785 19.892 127.99 0.498 -0.002

4/28/2010 12:54:12 6.436 12.805 17.827 93.07 0.605 -0.014

4/28/2010 12:55:12 6.293 12.916 17.146 87.71 0.634 0.021

4/28/2010 12:56:12 6.293 12.913 16.018 73.43 0.592 0.007

4/28/2010 12:57:12 6.421 12.806 20.453 104.19 0.592 0.003

4/28/2010 12:58:12 6.558 12.73 20.044 70.39 0.593 0.004

4/28/2010 12:59:12 6.479 12.789 19.257 42.9 0.576 0.004

4/28/2010 13:00:12 6.352 12.891 20.414 45.32 0.576 0.003

4/28/2010 13:01:13 6.468 12.799 21.707 42.35 0.576 0.003

4/28/2010 13:02:13 6.446 12.833 22.262 35.47 0.601 0.003

4/28/2010 13:03:13 6.379 12.874 22.957 43.23 0.586 0.004

4/28/2010 13:04:13 6.453 12.811 26.56 51.29 0.589 0.004

4/28/2010 13:05:13 6.508 12.786 22.039 38.76 0.596 0.003

4/28/2010 13:06:13 6.396 12.876 20.804 35.66 0.576 0.003

4/28/2010 13:07:13 6.295 12.942 22.021 46.16 0.576 0.003

4/28/2010 13:08:13 6.417 12.856 24.51 58.83 0.603 0.01

4/28/2010 13:09:13 6.584 12.742 20.188 34.91 0.63 0.022

4/28/2010 13:10:13 6.281 12.96 19.974 30.18 0.637 0.024

4/28/2010 13:11:13 6.314 12.942 21.95 34.25 0.636 0.034

4/28/2010 13:12:13 6.569 12.752 21.155 29.33 0.622 0.014

4/28/2010 13:13:13 6.431 12.854 21.428 26.95 0.575 0.003

4/28/2010 13:14:13 6.253 12.99 23.726 29.27 0.576 0.003

4/28/2010 13:15:13 6.477 12.809 24.136 33.3 0.576 0.003

4/28/2010 13:16:13 6.45 12.848 23.866 31.45 0.575 0.003

4/28/2010 13:17:13 6.309 12.952 23.384 31.66 0.576 0.003

4/28/2010 13:18:13 6.316 12.937 27.645 34.34 0.575 0.003

4/28/2010 13:19:13 6.589 12.718 27.915 31.82 0.57 0.003

4/28/2010 13:20:13 6.487 12.809 28.286 29.53 0.545 0.003

4/28/2010 13:21:13 6.438 12.848 25.808 29.23 0.545 0.003

4/28/2010 13:22:13 6.318 12.946 26.18 29.54 0.545 0.003

4/28/2010 13:23:13 6.356 12.923 26.421 28.9 0.546 0.006

4/28/2010 13:24:13 6.384 12.902 25.996 28.89 0.532 0.003

4/28/2010 13:25:13 6.305 12.959 24.907 37.57 0.515 0.003

4/28/2010 13:26:13 6.442 12.858 23.064 36.17 0.515 0.003

4/28/2010 13:27:13 6.285 12.974 24.764 29.52 0.515 0.003

4/28/2010 13:28:13 6.331 12.921 24.832 30.71 0.488 0.003

4/28/2010 13:29:13 6.399 12.866 25.415 30.17 0.485 0.003

4/28/2010 13:30:13 6.548 12.741 28.442 27.9 0.485 0.003

4/28/2010 13:31:13 6.397 12.865 25.846 27.15 0.485 0.003

4/28/2010 13:32:13 6.406 12.856 25.568 28.07 0.485 0.003

4/28/2010 13:33:13 6.477 12.798 25.996 28.13 0.485 0.003

4/28/2010 13:34:13 6.388 12.861 26.053 27.13 0.485 0.003

4/28/2010 13:35:13 6.392 12.848 25.66 32.01 0.51 0.003

4/28/2010 13:36:13 6.499 12.774 24.25 31.27 0.495 0.003

4/28/2010 13:37:13 6.512 12.77 24.066 26.82 0.499 0.003

4/28/2010 13:38:13 6.444 12.809 22.608 26.26 0.506 0.003

4/28/2010 13:39:13 6.352 12.88 23.989 28.97 0.485 0.003

4/28/2010 13:40:13 6.398 12.838 22.091 30.46 0.485 0.003

4/28/2010 13:41:13 6.404 12.835 21.913 29.31 0.513 0.003

4/28/2010 13:42:13 6.301 12.921 22.141 30.51 0.515 0.003

# 4/28/2010 13:43:13 6.395 12.857 21.574 30.24 0.497 0.003

4/28/2010 13:44:13 6.506 12.772 20.747 27.21 0.485 0.003

4/28/2010 13:45:13 6.461 12.805 20.955 27.09 0.485 0.003

4/28/2010 13:46:13 6.403 12.852 20.232 29.5 0.485 0.003

4/28/2010 13:47:13 6.393 12.864 20.344 31.27 0.485 0.003

4/28/2010 13:48:13 6.455 12.823 19.558 30.87 0.485 0.003

4/28/2010 13:49:14 6.519 12.759 17.651 26.33 0.485 0.003

4/28/2010 13:50:14 6.385 12.86 20.434 30.5 0.485 0.003

4/28/2010 13:51:14 6.482 12.79 20.24 33.55 0.475 0.003

4/28/2010 13:52:14 6.605 12.707 20.169 26.69 0.46 0.003

4/28/2010 13:53:14 6.422 12.849 18.771 27.44 0.485 0.003

4/28/2010 13:54:14 6.434 12.842 21.254 27.17 0.485 0.003

4/28/2010 13:55:14 6.576 12.721 22.243 26.13 0.485 0.003

4/28/2010 13:56:14 6.396 12.869 23.692 26.68 0.485 0.003

4/28/2010 13:57:14 6.495 12.784 23.31 25.81 0.485 0.003

4/28/2010 13:58:14 6.418 12.847 23.191 25.48 0.485 0.003

4/28/2010 13:59:14 6.472 12.803 21.853 24.66 0.482 0.003

4/28/2010 14:00:14 6.614 12.697 22.821 24.12 0.456 0.003

4/28/2010 14:01:14 6.678 12.655 21.561 24.8 0.455 0.003

4/28/2010 14:02:14 6.459 12.819 18.651 24.29 0.456 0.003

4/28/2010 14:03:14 6.439 12.836 16.767 25.03 0.456 0.003

4/28/2010 14:04:14 6.518 12.784 15.149 24.6 0.456 0.003

4/28/2010 14:05:14 6.423 12.849 15.733 26.86 0.455 0.003

4/28/2010 14:06:14 6.505 12.777 15.145 27.39 0.456 0.003

4/28/2010 14:07:14 6.464 12.81 16.088 26.94 0.485 0.003

4/28/2010 14:08:14 6.627 12.681 15.636 26.94 0.485 0.003

4/28/2010 14:09:14 6.258 12.979 16.292 27.7 0.485 0.003

4/28/2010 14:10:14 6.375 12.873 16.829 28.01 0.485 0.003

4/28/2010 14:11:14 6.564 12.716 20.911 27.58 0.485 0.003

4/28/2010 14:12:14 6.615 12.665 17.726 27.2 0.485 0.003

4/28/2010 14:13:14 6.555 12.702 20.399 29.73 0.487 0.015

4/28/2010 14:14:14 6.43 12.8 19.316 29.76 0.432 0.013

4/28/2010 14:15:14 6.542 12.701 19.262 28 0.52 -0.011

4/28/2010 14:16:14 6.661 12.611 18.583 26.16 0.475 -0.017

4/28/2010 14:17:14 6.542 12.71 18.102 27 0.441 -0.012

4/28/2010 14:18:14 6.399 12.828 17.466 28.75 0.456 0.012

4/28/2010 14:19:12 6.368 12.863 18.246 33.12 0.456 0.021

4/28/2010 14:20:12 6.52 12.756 16.686 31.02 0.456 0.003

4/28/2010 14:21:12 6.601 12.697 17.267 27.89 0.456 0.003

4/28/2010 14:22:12 6.442 12.826 18.705 31.5 0.475 0.003

4/28/2010 14:23:12 6.477 12.775 21.515 32.21 0.471 0.003

4/28/2010 14:24:12 6.587 12.704 21.102 33.27 0.464 0.003

4/28/2010 14:25:12 6.607 12.707 17.594 29.62 0.481 0.003

4/28/2010 14:26:12 6.469 12.801 16.799 30.52 0.455 0.003

4/28/2010 14:27:12 6.534 12.755 15.637 34.23 0.483 0.003

4/28/2010 14:28:12 6.714 12.619 14.49 28.94 0.485 0.003

4/28/2010 14:29:13 6.623 12.68 13.513 26.93 0.485 0.003

4/28/2010 14:30:13 6.413 12.844 14.657 28.94 0.485 0.003

4/28/2010 14:31:13 6.528 12.757 14.762 31.11 0.485 0.003

4/28/2010 14:32:13 6.67 12.658 16.54 28.75 0.485 0.003

4/28/2010 14:33:13 6.401 12.873 16.216 30.27 0.485 0.003

4/28/2010 14:34:13 6.539 12.762 15.882 31.88 0.485 0.003

# 4/28/2010 14:35:13 6.542 12.763 15.008 33.83 0.506 0.003

4/28/2010 14:36:13 6.432 12.845 15.427 30.59 0.515 0.003

4/28/2010 14:37:13 6.516 12.787 15.891 30.07 0.515 0.003

4/28/2010 14:38:13 6.572 12.742 13.83 27.77 0.52 0.003

4/28/2010 14:39:13 6.51 12.791 7.367 27.28 0.545 0.003

4/28/2010 14:40:13 6.524 12.789 3.769 27.5 0.516 0.003

4/28/2010 14:41:13 6.56 12.743 2.735 27.76 0.515 0.003

4/28/2010 14:42:13 6.518 12.789 3.086 29.01 0.496 0.003

4/28/2010 14:43:13 6.417 12.873 3.604 33.44 0.485 0.003

4/28/2010 14:44:13 6.591 12.738 3.668 32.31 0.485 0.003

4/28/2010 14:45:13 6.76 12.607 3.772 29.96 0.482 0.003

4/28/2010 14:46:13 6.583 12.74 5.404 28.38 0.455 0.003

4/28/2010 14:47:13 6.522 12.775 5.612 31.54 0.456 0.003

4/28/2010 14:48:13 6.686 12.643 4.536 30.83 0.456 0.003

4/28/2010 14:49:13 6.567 12.729 4.195 35.03 0.456 0.003

4/28/2010 14:50:13 6.487 12.797 3.898 40.2 0.455 0.003

4/28/2010 14:51:13 6.346 12.918 3.593 46.81 0.456 0.003

4/28/2010 14:52:13 6.531 12.767 4.319 45.47 0.456 0.003

Average of Test Run O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 14:52:13 6.468 12.808 18.763 34.12 0.509 0.004

Test Run 2 End

# Final System Bias Check for Run 2 . STRATA Version 3.2

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 14:55:08 14.348 5.797 4.713 88.91 0.502 0.004

4/28/2010 14:56:08 20.729 0.201 0.221 12.73 2.827 0.003

4/28/2010 14:57:08 20.749 0.175 -0.441 2.32 6.816 3.869

4/28/2010 14:58:08 10.039 0.164 -0.675 2.07 6.791 6.446

4/28/2010 14:59:08 0.187 0.153 -0.74 2.07 5.95 6.292

4/28/2010 15:00:08 0.155 0.147 -0.829 2.12 1.196 5.401

4/28/2010 15:01:08 3.242 3.365 -0.821 2.14 0.245 0.003

4/28/2010 15:02:08 9.873 10.148 -0.909 1.75 0.245 0.003

4/28/2010 15:03:08 2.23 2.185 13.633 1.69 0.245 0.003

4/28/2010 15:04:08 0.153 0.152 34.771 2.07 0.245 0.003

4/28/2010 15:05:08 0.147 0.132 37.771 2.07 0.245 0.003

4/28/2010 15:06:08 0.146 0.123 38.993 2.07 0.245 0.003

4/28/2010 15:07:08 0.144 0.118 39.471 2.07 0.268 0.003

4/28/2010 15:08:08 0.145 0.115 39.765 2.06 0.275 0.003

4/28/2010 15:09:08 0.144 0.11 40.002 2.07 0.275 0.003

4/28/2010 15:10:08 4.89 0.115 38.454 14.14 0.275 0.003

4/28/2010 15:11:08 20.621 0.116 6.584 182 0.276 0.003

Final System Bias Check for Run 2

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

CO CC281576 CC41590

CH4 CC281576 CC178755

NMHC CC281576 CC178755

Date/Time 4/28/2010 15:11:42 PASSED

Analyte O2 CO2 SO2 CO CH4 NMHC

Units % % ppm ppm ppm ppm

Zero Ref Cyl 000000

Zero Cal 0.061 0.019 -0.194 -0.17 0.364 0.003

Zero Avg 0.15 0.14 -0.901 2.05 0.245 0.003

Zero Bias% 0.4 0.7 0.8 1.1 0.5 0

Zero Drift% 0 0.3 -1.3 -0.4 -0.6 0

Span Ref Cyl 9.993 10 45.2 201 7.049 7.001

Span Cal 9.959 10.206 44.566 202.5 7.093 6.836

Span Avg 9.877 10.156 40.242 205.21 6.804 6.446

Span Bias% 0.4 0.3 4.8 1.3 1.1 1.6

Span Drift% 0 0 -0.2 -1 -0.7 -0.7

Ini Zero Avg 0.16 0.091 0.283 2.91 0.395 0.003

Ini Span Avg 9.88 10.153 40.38 207.21 6.973 6.626

Run Avg 6.468 12.808 18.763 34.12 0.509 0.004

Co 0.155 0.116 -0.309 2.48 0.32 0.003

Cm 9.878 10.154 40.311 206.21 6.889 6.536

Correct Avg 6.488 12.643 21.222 31.21 0.202 0.001

# Calibration Error Test at Run 3 . STRATA Version 3.2

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 15:13:31 0.083 0.086 -1.746 6.95 0.297 0.003

4/28/2010 15:14:31 7.268 5.996 -0.194 0.02 0.605 0.003

4/28/2010 15:15:31 17.388 14.829 -0.151 -0.05 1.335 0.003

4/28/2010 15:16:31 4.945 5.409 24.212 10.29 1.329 0.003

4/28/2010 15:17:31 0.069 0.102 87.487 4.31 0.96 0.003

4/28/2010 15:18:31 0.063 0.098 89.207 0.05 0.654 0.003

4/28/2010 15:19:31 0.064 0.097 64.121 -0.06 0.636 0.003

4/28/2010 15:20:31 10.767 0.101 29.989 52.59 0.636 0.003

4/28/2010 15:21:31 20.921 0.099 -0.058 197.95 0.636 0.003

4/28/2010 15:22:31 20.815 0.105 0.157 126.67 0.61 0.003

4/28/2010 15:23:31 20.927 0.099 -0.159 93.57 0.625 0.003

4/28/2010 15:24:31 12.419 7.816 3.93 96.52 0.65 0.004

4/28/2010 15:25:31 15.147 4.435 6.256 63.39 0.612 0.003

4/28/2010 15:26:31 2.262 0.164 1.954 10.65 0.461 0.003

4/28/2010 15:27:31 3.136 0.143 1.438 2.32 0.305 0.003

4/28/2010 15:28:31 20.684 0.138 1.304 2.08 0.249 0.003

4/28/2010 15:29:32 20.749 0.134 1.22 1.86 18.594 0.003

4/28/2010 15:30:32 20.763 0.131 1.137 1.86 24.263 23.178

4/28/2010 15:31:32 20.775 0.128 1.101 1.85 24.389 24.025

4/28/2010 15:32:32 20.78 0.128 1.091 1.85 24.479 24.17

4/28/2010 15:33:32 20.782 0.125 1.138 1.86 24.749 24.247

4/28/2010 15:34:32 20.787 0.123 1.035 1.87 25.377 24.55

4/28/2010 15:35:32 20.742 0.122 1.116 1.87 25.319 24.848

4/28/2010 15:36:32 20.761 0.122 1.068 1.86 14.29 24.057

4/28/2010 15:37:32 20.754 0.122 0.934 1.87 12.087 11.75

4/28/2010 15:38:32 20.778 0.117 0.955 1.87 9.599 11.723

Calibration Error Test at Run 3

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Low-range Mid-range High-range

O2 CC281576 SG9135786 CC285394

CO2 CC281576 SG9135786 CC285394

SO2 CC281576 CC308434 CC122146

CO CC281576 CC91533 CC41590

CH4 CC281576 CC178755 CC245119 CC155902

NMHC CC281576 CC178755 CC245119 CC155902

Date/Time 4/28/2010 15:39:04 PASSED

Analyte O2 CO2 SO2 CO CH4 NMHC

Units % % ppm ppm ppm ppm

Zero Ref Cyl 0 0 0 0 0 0

Zero Avg 0.069 0.086 -0.133 -0.09 0.305 0.003

Zero Error% 0.3 0.5 0.1 0 1.2 0

Low Ref Cyl 7.049 7.001

Low Avg 7.122 6.717

Low Error% 0.3 1.1

Mid Ref Cyl 9.993 10 45.2 90.16 12.05 12.03

Mid Avg 9.981 10.291 45.239 93.32 12.106 11.75

Mid Error% 0.1 1.6 0 1.6 0.2 1.1

High Ref Cyl 22 17.76 91.01 201 25.37 24.86

High Avg 22.036 17.898 91.391 203.65 25.379 24.816

High Error% 0.2 0.8 0.4 1.3 0 0.2

# Initial System Bias Check for Run 3 . STRATA Version 3.2

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 15:40:07 12.009 0.115 0.909 1.85 7.096 6.708

4/28/2010 15:41:08 0.193 0.11 0.891 1.98 2.32 6.656

4/28/2010 15:42:08 1.588 1.649 0.962 1.98 0.259 0.225

4/28/2010 15:43:08 9.876 10.117 0.899 1.63 0.246 0.004

4/28/2010 15:44:08 2.797 2.752 15.144 1.49 0.251 0.003

4/28/2010 15:45:08 0.151 0.139 37.85 2.01 0.275 0.003

4/28/2010 15:46:08 0.142 0.123 40.972 1.86 0.245 0.003

4/28/2010 15:47:08 0.718 0.124 42.3 1.87 0.245 0.003

4/28/2010 15:48:08 20.434 0.117 13.678 151.55 0.245 0.003

Initial System Bias Check for Run 3

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

CO CC281576 CC41590

CH4 CC281576 CC178755

NMHC CC281576 CC178755

Date/Time 4/28/2010 15:48:26 PASSED

Analyte O2 CO2 SO2 CO CH4 NMHC

Units % % ppm ppm ppm ppm

Zero Ref Cyl 000000

Zero Cal 0.069 0.086 -0.133 -0.09 0.305 0.003

Zero Avg 0.158 0.11 0.96 1.8 0.275 0.004

Zero Bias% 0.4 0.1 1.2 0.9 0.1 0

Zero Drift%

Span Ref Cyl 9.993 10 45.2 201 7.049 7.001

Span Cal 9.981 10.291 45.239 203.65 7.122 6.717

Span Avg 9.89 10.14 42.322 204.34 7.121 6.716

Span Bias% 0.4 0.9 3.2 0.3 0 0

Span Drift%

# Test Run 3 Begin. STRATA Version 3.2

Operator: M. Martin

Plant Nam e Dominion Southampton

Location: Common Stack

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 15:49:27 13.186 7.004 7.908 160.23 0.269 0.003

Begin calculating run averages

4/28/2010 15:51:03 6.378 12.871 6.705 38.42 0.515 0.003

4/28/2010 15:52:03 6.199 13.027 6.227 38.34 0.515 0.003

4/28/2010 15:53:01 6.418 12.852 5.653 33.75 0.515 0.003

4/28/2010 15:54:01 6.466 12.812 6.835 30.91 0.495 0.003

4/28/2010 15:55:01 6.178 13.052 6.628 34.98 0.485 0.003

4/28/2010 15:56:01 6.458 12.836 6.728 34.82 0.485 0.003

4/28/2010 15:57:01 6.529 12.786 6.498 31.89 0.481 0.003

4/28/2010 15:58:01 6.479 12.827 6.328 28.28 0.455 0.003

4/28/2010 15:59:01 6.445 12.838 6.569 31.7 0.455 0.003

4/28/2010 16:00:01 6.427 12.858 6.201 39.62 0.456 0.003

4/28/2010 16:01:01 6.429 12.863 6.329 36.17 0.472 0.003

4/28/2010 16:02:02 6.396 12.893 6.763 39.43 0.485 0.003

4/28/2010 16:03:02 6.286 12.985 7.116 44.43 0.478 0.003

4/28/2010 16:04:02 6.279 12.983 6.407 41.45 0.455 0.003

4/28/2010 16:05:02 6.416 12.869 10.587 46.8 0.455 0.003

4/28/2010 16:06:02 6.434 12.866 8.92 37.75 0.481 0.003

4/28/2010 16:07:02 6.522 12.783 8.603 41.71 0.485 0.003

4/28/2010 16:08:02 6.224 13.023 6.896 49.68 0.485 0.003

4/28/2010 16:09:02 6.332 12.942 5.958 44.25 0.485 0.003

4/28/2010 16:10:02 6.408 12.889 5.141 33.68 0.485 0.003

4/28/2010 16:11:02 6.382 12.905 5.362 30.58 0.485 0.003

4/28/2010 16:12:02 6.324 12.948 5.89 35.07 0.485 0.003

4/28/2010 16:13:02 6.359 12.918 6.902 39.2 0.485 0.003

4/28/2010 16:14:02 6.412 12.879 7.013 35.91 0.504 0.003

4/28/2010 16:15:02 6.446 12.865 7.391 33.73 0.502 0.003

4/28/2010 16:16:02 6.396 12.905 7.68 32.66 0.485 0.003

4/28/2010 16:17:02 6.488 12.812 9.034 36.96 0.485 0.003

4/28/2010 16:18:02 6.415 12.872 11.228 44.32 0.485 0.003

4/28/2010 16:19:02 6.519 12.813 10.631 40.78 0.458 0.003

4/28/2010 16:20:02 6.445 12.881 10.36 29.89 0.476 0.003

4/28/2010 16:21:02 6.394 12.896 10.107 29.97 0.469 0.003

4/28/2010 16:22:02 6.435 12.875 11.32 29.53 0.455 0.003

4/28/2010 16:23:02 6.479 12.845 9.692 25.76 0.461 0.003

4/28/2010 16:24:02 6.525 12.812 9.005 25.46 0.485 0.003

4/28/2010 16:25:02 6.537 12.8 8.849 25.7 0.485 0.003

4/28/2010 16:26:02 6.364 12.934 9.666 28.35 0.485 0.003

4/28/2010 16:27:02 6.298 12.984 9.469 27.55 0.485 0.003

4/28/2010 16:28:02 6.6 12.747 9.61 26.26 0.499 0.003

4/28/2010 16:29:02 6.616 12.739 9.663 24.88 0.515 0.003

4/28/2010 16:30:02 6.439 12.876 8.655 24.46 0.515 0.003

4/28/2010 16:31:02 6.34 12.953 7.67 25.35 0.515 0.003

4/28/2010 16:32:02 6.5 12.833 7.063 26.95 0.515 0.003

4/28/2010 16:33:02 6.505 12.835 6.679 26.29 0.515 0.003

4/28/2010 16:34:02 6.546 12.797 6.204 26.67 0.515 0.003

# 4/28/2010 16:35:02 6.567 12.769 5.743 28.84 0.515 0.003

4/28/2010 16:36:02 6.246 13.03 5.046 30.63 0.521 0.003

4/28/2010 16:37:02 6.383 12.91 6.59 33.73 0.544 0.003

4/28/2010 16:38:02 6.629 12.719 10.454 30.16 0.515 0.003

4/28/2010 16:39:02 6.431 12.885 9.35 29.08 0.541 0.003

4/28/2010 16:40:02 6.427 12.883 9.166 30.7 0.525 0.003

4/28/2010 16:41:02 6.403 12.899 9.039 32.12 0.515 0.003

4/28/2010 16:42:02 6.513 12.806 8.616 32.53 0.515 0.003

4/28/2010 16:43:02 6.571 12.761 7.977 29.6 0.515 0.003

4/28/2010 16:44:02 6.496 12.812 7.828 28.93 0.515 0.004

4/28/2010 16:45:02 6.426 12.861 7.634 29.74 0.516 0.004

4/28/2010 16:46:02 6.457 12.841 7.661 28.31 0.516 0.004

4/28/2010 16:47:02 6.427 12.874 6.175 26.71 0.515 0.004

4/28/2010 16:48:02 6.584 12.739 10.039 27.7 0.515 0.003

4/28/2010 16:49:03 6.459 12.849 10.594 27.44 0.522 0.004

4/28/2010 16:50:03 6.429 12.872 10.733 29.76 0.543 0.003

4/28/2010 16:51:03 6.598 12.743 9.756 27.98 0.515 0.003

4/28/2010 16:52:03 6.686 12.674 8.771 26.09 0.542 0.003

4/28/2010 16:53:03 6.518 12.804 8.867 28.98 0.545 0.003

4/28/2010 16:54:03 6.5 12.813 9.449 29.15 0.545 0.003

4/28/2010 16:55:03 6.623 12.726 9.083 27.33 0.545 0.003

4/28/2010 16:56:03 6.616 12.735 8.158 25.59 0.545 0.003

4/28/2010 16:57:03 6.446 12.867 7.197 28.16 0.545 0.003

4/28/2010 16:58:03 6.503 12.835 6.421 28.06 0.545 0.003

4/28/2010 16:59:03 6.542 12.797 5.907 28.77 0.545 0.003

4/28/2010 17:00:03 6.59 12.764 6.154 29.28 0.545 0.003

4/28/2010 17:01:03 6.497 12.842 6.549 28.71 0.545 0.003

4/28/2010 17:02:03 6.665 12.716 6.9 27.36 0.546 0.004

4/28/2010 17:03:03 6.628 12.735 6.254 26.84 0.546 0.003

4/28/2010 17:04:03 6.535 12.794 7.391 29.33 0.546 0.003

4/28/2010 17:05:03 6.514 12.806 7.878 28.71 0.545 0.003

4/28/2010 17:06:03 6.615 12.72 7.283 28.95 0.546 0.004

4/28/2010 17:07:03 6.655 12.68 7.1 27.83 0.546 0.004

4/28/2010 17:08:03 6.444 12.855 6.904 27.38 0.547 0.003

4/28/2010 17:09:03 6.449 12.847 6.513 27.06 0.547 0.003

4/28/2010 17:10:03 6.596 12.727 6.555 27.65 0.545 0.003

4/28/2010 17:11:03 6.643 12.711 6.535 28.54 0.545 0.003

4/28/2010 17:12:03 6.57 12.777 6.872 26.85 0.545 0.003

4/28/2010 17:13:03 6.557 12.787 6.194 26.05 0.545 0.003

4/28/2010 17:14:03 6.516 12.822 6.425 27.17 0.53 0.003

4/28/2010 17:15:03 6.552 12.798 6.853 27.71 0.525 0.003

4/28/2010 17:16:03 6.521 12.813 7.522 27.55 0.545 0.003

4/28/2010 17:17:03 6.614 12.743 7.217 28.45 0.545 0.003

4/28/2010 17:18:03 6.699 12.668 7.307 28.2 0.545 0.003

4/28/2010 17:19:03 6.526 12.813 6.777 28.57 0.545 0.003

4/28/2010 17:20:03 6.555 12.778 5.852 31.87 0.545 0.003

4/28/2010 17:21:01 6.712 12.645 6.237 33.89 0.545 0.003

4/28/2010 17:22:01 6.514 12.814 5.476 36.45 0.545 0.003

4/28/2010 17:23:01 6.412 12.903 4.457 40.47 0.543 0.003

4/28/2010 17:24:01 6.409 12.909 3.937 40.72 0.515 0.003

4/28/2010 17:25:01 6.487 12.835 3.8 40.83 0.541 0.003

4/28/2010 17:26:01 6.596 12.757 3.923 43.04 0.545 0.003

# 4/28/2010 17:27:01 6.458 12.864 4.605 45.46 0.545 0.003

4/28/2010 17:28:01 6.437 12.876 4.691 53.4 0.545 0.003

4/28/2010 17:29:01 6.471 12.863 5.341 56.31 0.545 0.003

4/28/2010 17:30:01 6.387 12.942 5.599 45.15 0.545 0.003

4/28/2010 17:31:01 6.493 12.84 5.36 46.15 0.545 0.003

4/28/2010 17:32:01 6.606 12.756 7.033 44.56 0.545 0.003

4/28/2010 17:33:01 6.512 12.844 6.096 35.78 0.545 0.003

4/28/2010 17:34:01 6.501 12.841 5.965 38.96 0.545 0.003

4/28/2010 17:35:01 6.637 12.732 5.796 41.21 0.545 0.003

4/28/2010 17:36:01 6.524 12.823 5.651 41.86 0.546 0.003

4/28/2010 17:37:01 6.43 12.891 5.228 71.13 0.545 0.003

4/28/2010 17:38:01 6.523 12.818 5.128 83.14 0.545 0.003

4/28/2010 17:39:01 6.525 12.818 5.298 77.46 0.545 0.003

4/28/2010 17:40:01 6.406 12.915 5.109 110.1 0.545 0.003

4/28/2010 17:41:01 6.28 13.019 4.912 120.1 0.545 0.003

4/28/2010 17:42:02 6.416 12.901 6.91 110.98 0.55 0.005

4/28/2010 17:43:02 6.598 12.774 8.557 74.3 0.576 0.01

4/28/2010 17:44:02 6.517 12.852 6.104 53.67 0.545 0.003

4/28/2010 17:45:02 6.337 12.973 5.351 80.03 0.546 0.004

4/28/2010 17:46:02 6.338 12.974 4.725 74.44 0.545 0.003

4/28/2010 17:47:02 6.445 12.896 4.122 63.37 0.545 0.003

4/28/2010 17:48:02 6.506 12.847 3.965 58.25 0.545 0.003

4/28/2010 17:49:02 6.343 12.974 4.192 72.09 0.544 0.016

4/28/2010 17:50:02 6.457 12.897 4.871 83.59 0.515 0.003

Average of Test Run O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 17:50:02 6.476 12.842 7.084 38.53 0.52 0.003

Test Run 3 End

# Final System Bias Check for Run 3 . STRATA Version 3.2

O2 CO2 SO2 CO CH4 NMHC

% % ppm ppm ppm ppm

4/28/2010 17:51:08 6.454 12.904 4.972 67.87 0.546 0.003

4/28/2010 17:52:08 19.953 0.808 3.514 69.09 0.571 0.003

4/28/2010 17:53:08 20.725 0.228 1.592 3.84 5.116 0.003

4/28/2010 17:54:08 13.852 0.21 1.391 2.33 7.063 6.268

4/28/2010 17:55:08 0.196 0.199 1.278 2.21 4.81 6.738

4/28/2010 17:56:08 0.157 0.194 1.195 2.28 0.3 2.925

4/28/2010 17:57:09 8.251 8.602 1.136 2.1 0.275 0.003

4/28/2010 17:58:09 6.253 6.41 3.902 1.6 0.275 0.003

4/28/2010 17:59:09 0.161 0.234 33.362 1.96 0.275 0.003

4/28/2010 18:00:09 0.146 0.201 39.951 2.01 0.275 0.003

4/28/2010 18:01:09 0.142 0.195 41.735 2.01 0.274 0.002

4/28/2010 18:02:09 14.636 0.201 27.279 90.01 0.275 0.002

Final System Bias Check for Run 3

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

CO CC281576 CC41590

CH4 CC281576 CC178755

NMHC CC281576 CC178755

Date/Time 4/28/2010 18:03:07 PASSED

Analyte O2 CO2 SO2 CO CH4 NMHC

Units % % ppm ppm ppm ppm

Zero Ref Cyl 000000

Zero Cal 0.069 0.086 -0.133 -0.09 0.305 0.003

Zero Avg 0.148 0.194 1.231 2.28 0.304 0.003

Zero Bias% 0.4 0.6 1.5 1.2 0 0

Zero Drift% 0 0.5 0.3 0.2 0.1 0

Span Ref Cyl 9.993 10 45.2 201 7.049 7.001

Span Cal 9.981 10.291 45.239 203.65 7.122 6.717

Span Avg 9.871 10.251 42.05 205.11 7.063 6.716

Span Bias% 0.5 0.2 3.5 0.7 0.2 0

Span Drift% -0.1 0.6 -0.3 0.4 -0.2 0

Ini Zero Avg 0.158 0.11 0.96 1.8 0.275 0.004

Ini Span Avg 9.89 10.14 42.322 204.34 7.121 6.716

Run Avg 6.476 12.842 7.084 38.53 0.52 0.003

Co 0.153 0.152 1.095 2.04 0.29 0.003

Cm 9.88 10.196 42.186 204.73 7.092 6.716

Correct Avg 6.496 12.635 6.587 36.19 0.238 0

# Calibration Error Test at Run 1 . STRATA Version 3.2

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 7:04:57 4.072 0.85 2.858 -0.2

4/29/2010 7:05:57 0.054 0.289 2.443 0.3

4/29/2010 7:06:57 0.049 0.043 0.237 -0.51

4/29/2010 7:07:57 18.489 15.398 -0.021 -0.71

4/29/2010 7:08:57 15.191 13.324 -0.162 -0.6

4/29/2010 7:09:57 5.925 5.649 16.559 -0.45

4/29/2010 7:10:57 0.051 0.049 91.827 -0.45

4/29/2010 7:11:57 4.758 0.077 63.762 -0.68

4/29/2010 7:12:57 0.046 0.042 43.959 -0.71

4/29/2010 7:13:57 0.074 9.783 14.756 120.63

4/29/2010 7:14:57 0.026 11.305 1.701 447.05

4/29/2010 7:15:57 0.069 11.019 2.631 340.2

Calibration Error Test at Run 1

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Low-range Mid-range High-range

O2 CC281576 SG9135786 CC285394

CO2 CC281576 SG9135786 CC285394

SO2 CC281576 CC308434 CC122146

NOx CC281576 CC287768 SG9154467

Date/Time 4/29/2010 7:16:25 PASSED

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref Cyl 0 0 0 0

Zero Avg 0.046 0.043 -0.205 -0.71

Zero Error% 0.2 0.2 0.2 0.2

Low Ref Cyl

Low Avg

Low Error%

Mid Ref Cyl 9.993 10 45.2 187.1

Mid Avg 9.945 10.273 45.253 189.18

Mid Error% 0.2 1.5 0.1 0.5

High Ref Cyl 22 17.76 91.01 449.2

High Avg 22.005 17.827 91.574 449.22

High Error% 0 0.4 0.6 0

# Initial System Bias Check for Run 1 . STRATA Version 3.2

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 7:17:27 1.539 3.838 2.508 157.62

4/29/2010 7:18:27 0.143 0.083 3.151 50.17

4/29/2010 7:19:27 8.293 0.154 2.777 50.56

4/29/2010 7:20:27 5.285 0.287 0.808 11.84

4/29/2010 7:21:27 0.689 0.091 0.622 -0.14

4/29/2010 7:22:27 0.86 0.084 0.404 -0.32

4/29/2010 7:23:27 0.161 0.079 0.569 -0.44

4/29/2010 7:24:27 0.233 0.074 0.958 23.57

4/29/2010 7:25:27 8.691 8.924 0.52 24.3

4/29/2010 7:26:27 5.281 5.32 7.934 -0.08

4/29/2010 7:27:27 0.146 0.125 36.778 -0.13

4/29/2010 7:28:27 0.132 0.102 40.644 -0.43

4/29/2010 7:29:27 0.127 0.093 41.61 -0.44

4/29/2010 7:30:27 0.125 1.501 41.788 -0.68

4/29/2010 7:31:27 0.108 11.166 7.361 258.14

Initial System Bias Check for Run 1

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

NOx CC281576 SG9154467

Date/Time 4/29/2010 7:32:01 PASSED

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref Cyl 0000

Zero Cal 0.046 0.043 -0.205 -0.71

Zero Avg 0.14 0.076 0.419 -0.44

Zero Bias% 0.4 0.2 0.7 0.1

Zero Drift%

Span Ref Cyl 9.993 10 45.2 449.2

Span Cal 9.945 10.273 45.253 449.22

Span Avg 9.898 10.163 42.344 446.4

Span Bias% 0.2 0.6 3.2 0.6

Span Drift%

# Test Run 1 Begin. STRATA Version 3.2

Operator: M. Martin

Plant Nam e Dominion Southampton

Location: Common Stack

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 7:33:02 11.258 5.246 1.738 380.36

4/29/2010 7:34:02 18.612 2.042 1.675 66.33

4/29/2010 7:35:02 6.685 12.626 0.979 187.08

4/29/2010 7:36:02 6.79 12.556 1.212 232.83

4/29/2010 7:37:02 6.699 12.621 2.464 226.53

4/29/2010 7:38:02 6.618 12.684 3.944 224.71

4/29/2010 7:39:02 6.801 12.536 3.749 223.13

4/29/2010 7:40:02 6.796 12.552 3.74 222.15

4/29/2010 7:41:02 6.533 12.738 6.203 222.78

4/29/2010 7:42:02 6.582 12.695 8.896 222.56

4/29/2010 7:43:02 6.728 12.586 11.051 221.91

4/29/2010 7:44:02 6.683 12.613 10.882 221.82

4/29/2010 7:45:02 6.719 12.573 15.435 223.36

4/29/2010 7:46:02 6.602 12.682 12.956 225.7

4/29/2010 7:47:03 6.794 12.515 12.662 227.21

4/29/2010 7:48:03 6.794 12.519 11.381 225.54

4/29/2010 7:49:03 6.772 12.534 10.89 226.7

4/29/2010 7:50:03 6.684 12.596 11.06 227.19

Begin calculating run averages

4/29/2010 7:51:19 6.661 12.624 12.907 227.48

4/29/2010 7:52:17 6.738 12.57 11.758 226.88

4/29/2010 7:53:17 6.744 12.57 12.538 226.94

4/29/2010 7:54:17 6.599 12.694 13.878 227.93

4/29/2010 7:55:17 6.64 12.661 14.368 228.3

4/29/2010 7:56:17 6.608 12.709 15.427 227.37

4/29/2010 7:57:17 6.637 12.695 16.52 228.06

4/29/2010 7:58:17 6.778 12.602 17.84 226.13

4/29/2010 7:59:17 6.718 12.672 19.421 225.19

4/29/2010 8:00:17 6.627 12.761 18.458 226.46

4/29/2010 8:01:17 6.724 12.683 17.42 225.61

4/29/2010 8:02:17 6.759 12.622 17.413 223.21

4/29/2010 8:03:17 6.712 12.656 17.144 222.14

4/29/2010 8:04:17 6.555 12.782 16.3 221.54

4/29/2010 8:05:17 6.633 12.724 15.737 221.64

4/29/2010 8:06:17 6.705 12.68 15.387 221.31

4/29/2010 8:07:18 6.553 12.796 16.032 221.56

4/29/2010 8:08:18 6.51 12.816 16.982 221.63

4/29/2010 8:09:18 6.724 12.657 16.254 221.16

4/29/2010 8:10:18 6.806 12.613 13.495 219.47

4/29/2010 8:11:18 6.562 12.812 13.729 219.04

4/29/2010 8:12:18 6.377 12.96 12.991 220.61

4/29/2010 8:13:18 6.818 12.606 18.41 219.97

4/29/2010 8:14:18 6.721 12.702 17.999 218.03

4/29/2010 8:15:18 6.659 12.743 18.375 218.34

4/29/2010 8:16:18 6.558 12.82 18.94 218.71

4/29/2010 8:17:18 6.666 12.757 18.931 218.97

# 4/29/2010 8:18:18 6.792 12.666 19.235 219.23

4/29/2010 8:19:18 6.744 12.702 23.048 219.4

4/29/2010 8:20:18 6.876 12.61 23.673 220.61

4/29/2010 8:21:18 6.789 12.666 19.739 220.64

4/29/2010 8:22:18 6.713 12.707 23.261 221.17

4/29/2010 8:23:18 6.809 12.645 24.252 221.69

4/29/2010 8:24:18 6.814 12.676 22.707 220.77

4/29/2010 8:25:18 6.737 12.762 22.839 221.38

4/29/2010 8:26:18 6.87 12.679 21.72 221.08

4/29/2010 8:27:18 6.746 12.77 20.969 220.64

4/29/2010 8:28:18 6.724 12.771 22.133 222.3

4/29/2010 8:29:18 6.726 12.786 23.37 222.46

4/29/2010 8:30:18 6.715 12.793 22.437 220.97

4/29/2010 8:31:18 6.83 12.666 19.769 220.57

4/29/2010 8:32:18 6.786 12.714 18.051 220.78

4/29/2010 8:33:18 6.661 12.827 16.655 220.91

4/29/2010 8:34:18 6.853 12.677 15.891 220.69

4/29/2010 8:35:18 6.819 12.724 14.956 218.82

4/29/2010 8:36:18 6.697 12.852 14.073 219.39

4/29/2010 8:37:18 6.757 12.788 15.297 220.22

4/29/2010 8:38:18 6.669 12.851 15.242 219.86

4/29/2010 8:39:18 6.807 12.745 15.225 220.28

4/29/2010 8:40:18 6.867 12.711 16.482 219.19

4/29/2010 8:41:18 6.823 12.785 15.86 218.22

4/29/2010 8:42:18 6.828 12.829 15.121 218.53

4/29/2010 8:43:18 6.867 12.751 14.562 219.27

4/29/2010 8:44:18 6.813 12.818 13.578 219.61

4/29/2010 8:45:18 6.713 12.927 12.514 220.75

4/29/2010 8:46:18 6.692 13.066 13.006 222.3

4/29/2010 8:47:18 6.749 13.265 12.095 222.1

4/29/2010 8:48:18 6.706 13.434 11.501 221.51

4/29/2010 8:49:18 6.614 14.242 12.045 222.46

4/29/2010 8:50:18 6.776 13.222 12.12 222.16

4/29/2010 8:51:18 6.854 12.693 12.411 221.42

4/29/2010 8:52:19 6.886 11.939 11.315 222.72

4/29/2010 8:53:19 6.795 12.644 10.012 222.55

4/29/2010 8:54:19 6.708 11.745 8.648 222.98

4/29/2010 8:55:19 6.656 12.04 8.356 223.28

4/29/2010 8:56:19 6.72 12.18 8.369 223.75

4/29/2010 8:57:19 6.748 13.727* 8.598 224.08

4/29/2010 8:58:19 6.738 11.588 8.506 223.88

4/29/2010 8:59:19 6.573 11.784 9.692 224.45

4/29/2010 9:00:19 6.602 11.896 9.573 226.78

4/29/2010 9:01:19 6.82 12.721* 10.149 224.85

4/29/2010 9:02:19 6.816 12.286 13.69 224.16

4/29/2010 9:03:19 6.732 14.956* 11.009 226.04

4/29/2010 9:04:19 6.811 14.791 9.675 226.65

4/29/2010 9:05:19 6.71 14.259 9.456 227.31

4/29/2010 9:06:17 6.809 14.098 9.991 228.55

4/29/2010 9:07:17 6.784 14.095 9.628 227.73

4/29/2010 9:08:17 6.695 14.153 10.054 227.34

4/29/2010 9:09:17 6.787 14.068 10.459 227.51

# 4/29/2010 9:10:17 6.684 14.152 11.153 228.98

4/29/2010 9:11:18 6.694 14.083 11.946 230.37

4/29/2010 9:12:18 6.945 13.801 13.291 229.51

4/29/2010 9:13:18 6.957 13.792 14.705 227.5

4/29/2010 9:14:18 6.835 13.897 11.178 228.74

4/29/2010 9:15:18 6.719 13.988 9.955 229.77

4/29/2010 9:16:18 6.822 13.894 8.568 229.31

4/29/2010 9:17:18 6.808 13.911 8.491 227.88

4/29/2010 9:18:18 6.709 13.994 8.558 228.12

4/29/2010 9:19:18 6.737 13.97 9.008 229.31

4/29/2010 9:20:18 6.869 13.875 9.192 229

Pause

4/29/2010 9:21:18 3.814 7.495 7.652 205.93

4/29/2010 9:22:18 0.14 0.906 2.551 31.47

4/29/2010 9:23:18 0.133 0.87 1.362 1.23

4/29/2010 9:24:18 0.13 0.859 0.982 0.87

4/29/2010 9:25:18 0.128 0.854 0.841 0.47

4/29/2010 9:26:18 2.522 5.623 1.025 4.09

4/29/2010 9:27:18 8.193 12.307 4.904 201.92

4/29/2010 9:28:18 9.875 11.488 1.986 19.83

4/29/2010 9:29:19 9.885 11.5 0.992 0

4/29/2010 9:30:19 9.607 11.012 0.717 -0.13

4/29/2010 9:31:19 0.121 0.844 -0.652 -0.13

4/29/2010 9:32:19 0.059 0.333 -0.975 -0.38

4/29/2010 9:33:19 0.053 0.045 -1.037 -0.44

4/29/2010 9:34:19 0.048 0.047 -1.06 -0.44

4/29/2010 9:35:19 9.573 8.19 -1.099 -0.44

4/29/2010 9:36:19 22.013 17.849 -1.087 -0.44

4/29/2010 9:37:19 22.035 17.871 -1.179 -0.44

4/29/2010 9:38:19 22.047 17.88 -1.079 -0.44

4/29/2010 9:39:19 14.343 12.996 -1.118 -0.44

4/29/2010 9:40:19 9.966 10.433 -1.103 -0.44

4/29/2010 9:41:19 9.961 10.434 -1.191 -0.44

4/29/2010 9:42:19 8.264 8.496 -1.122 -0.44

4/29/2010 9:43:19 0.051 0.1 -1.162 -0.21

4/29/2010 9:44:19 3.962 3.409 -1.193 -0.44

4/29/2010 9:45:19 22.016 17.684 -1.294 -0.44

4/29/2010 9:46:19 22.039 17.477 -1.341 -0.44

4/29/2010 9:47:19 22.045 17.481 -1.221 -0.44

4/29/2010 9:48:19 20.468 16.404 -1.391 -0.45

4/29/2010 9:49:19 9.966 10.211 -1.28 -0.44

4/29/2010 9:50:19 9.956 10.206 -1.231 -0.44

4/29/2010 9:51:19 9.948 10.205 -1.367 -0.44

4/29/2010 9:52:19 9.948 10.207 -1.427 -0.44

4/29/2010 9:53:19 9.945 10.207 -1.303 -0.44

4/29/2010 9:54:19 5.78 6.631 1.996 28.52

4/29/2010 9:55:19 0.146 0.2 0.91 1.37

4/29/2010 9:56:19 0.126 0.146 0.633 -0.7

4/29/2010 9:57:19 0.123 0.12 0.401 -0.92

4/29/2010 9:58:19 4.229 4.348 0.235 -1.01

4/29/2010 9:59:19 9.854 10.062 0.148 -1.01

4/29/2010 10:00:19 9.87 10.092 0.266 -1.01

# 4/29/2010 10:01:18 9.875 10.101 0.222 -1.01

4/29/2010 10:02:18 7.878 11.603 1.55 53.03

4/29/2010 10:03:18 6.591 12.513 6.384 234.12

End Pause

4/29/2010 10:04:18 6.807 12.345 7.662 230.77

4/29/2010 10:05:18 6.885 12.297 7.912 226.1

4/29/2010 10:06:18 6.807 12.352 7.786 226.36

4/29/2010 10:07:18 6.685 12.448 7.604 226.79

4/29/2010 10:08:18 6.802 12.362 7.245 227.04

4/29/2010 10:09:18 6.736 12.422 7.534 226.55

4/29/2010 10:10:18 6.688 12.446 7.558 226.4

4/29/2010 10:11:18 6.671 12.465 7.317 225.32

4/29/2010 10:12:18 6.83 12.346 7.891 224.77

4/29/2010 10:13:18 6.611 12.528 8.481 225.75

4/29/2010 10:14:18 6.601 12.522 8.396 227.55

4/29/2010 10:15:18 6.685 12.455 9.599 227.45

4/29/2010 10:16:18 6.695 12.465 9.059 227.76

4/29/2010 10:17:18 6.753 12.418 8.071 229.36

4/29/2010 10:18:18 6.736 12.427 6.775 228.9

4/29/2010 10:19:18 6.711 12.428 6.001 229.03

4/29/2010 10:20:18 6.627 12.488 5.113 230.25

4/29/2010 10:21:18 6.68 12.431 5.152 230.65

4/29/2010 10:22:18 6.842 12.308 5.039 229.82

4/29/2010 10:23:18 6.72 12.409 4.819 229.45

4/29/2010 10:24:18 6.495 12.585 4.933 231.2

4/29/2010 10:25:18 6.507 12.554 5.595 230.42

4/29/2010 10:26:18 6.859 12.26 6.813 227.72

4/29/2010 10:27:18 6.693 12.411 6.724 226.03

4/29/2010 10:28:18 6.592 12.479 5.784 228.81

4/29/2010 10:29:18 6.642 12.445 5.634 228.07

4/29/2010 10:30:19 6.767 12.344 5.445 227.35

4/29/2010 10:31:19 6.824 12.301 4.816 225.27

4/29/2010 10:32:19 6.627 12.456 4.288 224.24

4/29/2010 10:33:19 6.647 12.441 4.033 224.34

4/29/2010 10:34:19 6.637 12.456 3.698 224.59

4/29/2010 10:35:19 6.582 12.497 3.71 225.02

4/29/2010 10:36:19 6.673 12.43 5.843 224.3

4/29/2010 10:37:19 6.653 12.448 6.059 223.65

4/29/2010 10:38:19 6.695 12.423 5.467 224.1

4/29/2010 10:39:19 6.684 12.434 4.949 223.94

4/29/2010 10:40:19 6.635 12.473 5.097 224.76

4/29/2010 10:41:19 6.566 12.535 5.56 225.64

4/29/2010 10:42:19 6.654 12.46 5.461 226.62

4/29/2010 10:43:19 6.619 12.488 6.968 226.9

4/29/2010 10:44:19 6.496 12.591 5.657 228.06

4/29/2010 10:45:19 6.62 12.506 5.395 227.78

4/29/2010 10:46:19 6.67 12.454 5.694 225.41

4/29/2010 10:47:19 6.532 12.554 6.895 224.43

4/29/2010 10:48:19 6.524 12.564 6.491 223.94

4/29/2010 10:49:19 6.723 12.423 6.097 222.66

4/29/2010 10:50:19 6.545 12.566 5.851 223.25

4/29/2010 10:51:19 6.612 12.513 6.182 224.32

# 4/29/2010 10:52:19 6.645 12.481 6.053 224.11

4/29/2010 10:53:19 6.617 12.508 6.37 222.76

4/29/2010 10:54:19 6.531 12.58 6.327 222.12

4/29/2010 10:55:19 6.574 12.554 6.72 222.45

4/29/2010 10:56:19 6.56 12.58 5.729 222.3

4/29/2010 10:57:19 6.694 12.464 6.096 221.78

4/29/2010 10:58:19 6.615 12.542 6.432 222.02

4/29/2010 10:59:19 6.513 12.622 6.062 223.37

4/29/2010 11:00:19 6.568 12.587 6.006 224.9

4/29/2010 11:01:19 6.612 12.557 5.937 225.21

4/29/2010 11:02:19 6.592 12.573 5.339 225.11

4/29/2010 11:03:19 6.504 12.639 4.732 224.91

4/29/2010 11:04:19 6.411 12.714 4.652 226.03

4/29/2010 11:05:19 6.561 12.61 4.397 224.54

4/29/2010 11:06:19 6.485 12.678 4.096 223.34

4/29/2010 11:07:17 6.521 12.654 4.01 224.03

4/29/2010 11:08:17 6.488 12.675 5.14 223.89

4/29/2010 11:09:17 2.422 4.611 1.828 81.8

4/29/2010 11:10:17 0000

4/29/2010 11:11:17 0000

Pause

4/29/2010 11:12:18 0000

4/29/2010 11:13:18 0000

4/29/2010 11:14:18 0000

4/29/2010 11:15:18 0000

4/29/2010 11:16:18 0000

4/29/2010 11:17:19 0000

4/29/2010 11:18:19 0000

4/29/2010 11:19:19 0000

4/29/2010 11:20:19 0000

4/29/2010 11:21:19 0000

4/29/2010 11:22:19 0000

4/29/2010 11:23:19 0000

4/29/2010 11:24:19 0000

4/29/2010 11:25:19 0000

4/29/2010 11:26:19 0000

4/29/2010 11:27:19 0000

4/29/2010 11:28:19 0000

4/29/2010 11:29:19 12.163 -0.275 -0.124 6.9

4/29/2010 11:30:19 20.257 -0.455 -0.594 -0.94

4/29/2010 11:31:19 20.244 -0.452 -0.647 -0.93

4/29/2010 11:32:19 20.224 -0.443 -0.66 -0.94

4/29/2010 11:33:17 20.25 -0.451 -0.739 -0.94

4/29/2010 11:34:17 20.195 -0.408 -0.751 -0.94

4/29/2010 11:35:17 20.188 -0.406 -0.732 -0.94

4/29/2010 11:36:17 20.171 -0.393 -0.837 -0.94

4/29/2010 11:37:17 20.175 -0.405 -0.836 -0.94

4/29/2010 11:38:17 20.161 -0.392 -0.799 -0.94

4/29/2010 11:39:17 20.19 -0.425 -0.848 -0.94

4/29/2010 11:40:18 20.21 -0.445 -0.905 -0.94

4/29/2010 11:41:18 20.189 -0.432 -0.972 -0.94

4/29/2010 11:42:18 20.209 -0.451 -0.853 -0.94

# 4/29/2010 11:43:18 20.206 -0.45 -0.902 -0.94

4/29/2010 11:44:18 20.202 -0.45 -0.968 -0.94

4/29/2010 11:45:18 20.222 -0.465 -1.156 -0.94

4/29/2010 11:46:18 20.229 -0.475 -1.224 -0.94

4/29/2010 11:47:18 20.225 -0.48 -1.244 -0.94

4/29/2010 11:48:18 20.238 -0.495 -1.272 -0.94

4/29/2010 11:49:18 11.953 6.43 1.72 22.42

4/29/2010 11:50:18 6.599 10.589 7.613 233.49

End Pause

4/29/2010 11:51:18 6.533 10.631 8.253 231.84

4/29/2010 11:52:18 6.533 10.639 8.104 230.53

4/29/2010 11:53:18 6.638 10.536 7.935 230.74

4/29/2010 11:54:18 6.564 10.594 9.708 231.58

4/29/2010 11:55:18 6.571 10.59 7.621 233.84

4/29/2010 11:56:18 6.559 10.601 7.735 234.51

4/29/2010 11:57:18 6.571 10.586 7.409 235.24

4/29/2010 11:58:18 6.661 10.513 6.58 235.3

4/29/2010 11:59:18 6.507 10.619 6.837 236.42

4/29/2010 12:00:18 6.507 10.607 7.568 236.74

4/29/2010 12:01:18 6.679 10.472 7.65 234.84

4/29/2010 12:02:18 6.643 10.504 7.588 234.09

4/29/2010 12:03:18 6.503 10.601 7.781 234.46

4/29/2010 12:04:18 6.439 10.642 8.176 235.81

4/29/2010 12:05:18 6.514 10.591 7.954 236.58

4/29/2010 12:06:18 6.599 10.506 9.168 235.02

4/29/2010 12:07:18 6.603 10.505 10.27 234.32

4/29/2010 12:08:18 6.586 10.549 8.77 234.11

4/29/2010 12:09:18 6.569 10.56 8.222 234.89

4/29/2010 12:10:18 6.542 10.573 7.585 234.63

4/29/2010 12:11:18 6.636 10.496 10.351 232.97

4/29/2010 12:12:18 6.583 10.549 9.821 232.26

4/29/2010 12:13:18 6.615 10.527 8.515 232.37

Average of Test Run O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 12:13:36 6.681 12.301* 10.717 225.635

Test Run 1 End CO2 invalid

# Final System Bias Check for Run 1 . STRATA Version 3.2

O2 CO2 SO2 NOx O2

% % ppm ppm Volts

4/29/2010 12:14:43 4.149 4.697 7.161 196.8 1.6598

4/29/2010 12:15:43 0.128 -0.929 1.056 1.56 0.0514

4/29/2010 12:16:43 0.112 -0.959 0.045 0.36 0.0448

4/29/2010 12:17:43 9.336 7.777 -0.149 0.18 3.7345

4/29/2010 12:18:43 3.574 2.261 8.122 0.01 1.4295

4/29/2010 12:19:43 0.124 -0.874 34.175 -0.07 0.0496

4/29/2010 12:20:43 0.115 -0.894 38.508 -0.12 0.0462

4/29/2010 12:21:43 0.115 -0.899 39.679 -0.37 0.0459

4/29/2010 12:22:43 0.112 -0.905 40.476 -0.38 0.0448

4/29/2010 12:23:43 0.109 -0.905 40.663 -0.37 0.0435

4/29/2010 12:24:43 0.113 -0.906 40.608 -0.37 0.045

4/29/2010 12:25:43 0.111 1.332 39.938 -0.37 0.0445

4/29/2010 12:26:43 0.098 9.265 9.792 323.88 0.0392

Final System Bias Check for Run 1

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

NOx CC281576 SG9154467

Date/Time 4/29/2010 12:26:43 FAILED

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref Cyl 0000

Zero Cal 0.046 0.043 -0.205 -0.71

Zero Avg 0.108 -0.961 0.104 0.48

Zero Bias% 0.3 5.7 0.3 0.3

Zero Drift% -0.1 -5.8 -0.3 0.2

Span Ref Cyl 9.993 10 45.2 449.2

Span Cal 9.945 10.273 45.253 449.22

Span Avg 9.849 8.214 40.867 442.08

Span Bias% 0.4 11.6 4.8 1.6

Span Drift% -0.2 -11 -1.6 -1

Ini Zero Avg 0.14 0.076 0.419 -0.44

Ini Span Avg 9.898 10.163 42.344 446.4

Run Avg 6.579 12.301 10.562 222.16

Co 0.124 -0.443 0.262 0.02

Cm 9.874 9.189 41.606 444.24

Correct Avg 6.616 13.232 F 11.261 224.63

22 17.76 91.01 449.2

# Date/Time

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref Cyl 0000

Zero Cal 0.046 0.043 -0.205 -0.71

Zero Avg 0.108 -0.961 0.104 0.48

Zero Bias% 0.3 -5.7 0.3 0.3

Zero Drift% -0.1 -5.8 -0.3 0.2

Span Ref Cyl 9.993 10 45.2 449.2

Span Cal 9.945 10.273 45.253 449.22

Span Avg 9.849 8.214 40.867 442.08

Span Bias% -0.4 -11.6 -4.8 -1.6

Span Drift% -0.2 -11.0 -1.6 -1.0

Ini Zero Avg 0.14 0.076 0.419 -0.44

Ini Span Avg 9.898 10.163 42.344 446.4

Run Avg 6.681 12.301* 10.717 225.635

Co 0.124 -0.443 0.262 0.020

Cm 9.8735 9.1885 41.6055 444.24

Correct Avg 6.721 #VALUE! 11.430 228.144

# Calibration Error Test at Run 2 . STRATA Version 3.2

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 12:28:10 0.106 0.428 -0.24 292.5

4/29/2010 12:29:08 0.045 -0.328 -0.667 0.24

4/29/2010 12:30:08 20.645 15.472 -0.143 0.15

4/29/2010 12:31:08 16.093 13.652 -0.188 -0.07

4/29/2010 12:32:09 4.38 4.189 34.516 0.08

4/29/2010 12:33:09 0.044 -0.005 89.529 0.18

4/29/2010 12:34:09 0.043 0.427 66.598 1.42

4/29/2010 12:35:09 0.03 6.277 28.252 103.36

4/29/2010 12:36:09 0.025 10.913 1.603 446.81

Calibration Error Test at Run 2

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Low-range Mid-range High-range

O2 CC281576 SG9135786 CC285394

CO2 CC281576 SG9135786 CC285394

SO2 CC281576 CC308434 CC122146

NOx CC281576 CC287768 SG9154467

Date/Time 4/29/2010 12:37:03 PASSED

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref Cyl 0 0 0 0

Zero Avg 0.044 0.034 -0.14 0.18

Zero Error% 0.2 0.2 0.2 0

Low Ref Cyl

Low Avg

Low Error%

Mid Ref Cyl 9.993 10 45.2 187.1

Mid Avg 9.955 9.996 45.473 189.29

Mid Error% 0.2 0 0.3 0.5

High Ref Cyl 22 17.76 91.01 449.2

High Avg 22.025 17.447 91.47 452.08

High Error% 0.1 1.8 0.5 0.6

# Initial System Bias Check for Run 2 . STRATA Version 3.2

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 12:38:04 2.768 7.636 7.305 193.36

4/29/2010 12:39:04 0.109 0.119 3.333 47.71

4/29/2010 12:40:04 0.105 0.075 1.991 1.09

4/29/2010 12:41:04 1.476 1.505 1.517 0.66

4/29/2010 12:42:04 9.836 9.887 1.479 0.42

4/29/2010 12:43:04 2.752 2.701 14.552 0.7

4/29/2010 12:44:04 0.12 0.074 38.572 0.18

4/29/2010 12:45:04 0.107 0.054 41.572 0

4/29/2010 12:46:05 0.108 0.044 42.906 -0.07

4/29/2010 12:47:05 0.098 10.364 19.186 234.66

Initial System Bias Check for Run 2

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

NOx CC281576 SG9154467

Date/Time 4/29/2010 12:47:35 PASSED

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref Cyl 0000

Zero Cal 0.044 0.034 -0.14 0.18

Zero Avg 0.099 0.062 1.417 0.77

Zero Bias% 0.3 0.2 1.7 0.1

Zero Drift%

Span Ref Cyl 9.993 10 45.2 449.2

Span Cal 9.955 9.996 45.473 452.08

Span Avg 9.844 9.908 42.965 442.6

Span Bias% 0.5 0.5 2.8 2.1

Span Drift%

# Test Run 2 Begin. STRATA Version 3.2

Operator: M. Martin

Plant Nam e Dominion Southampton

Location: Common Stack

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 12:48:35 3.219 11.612 8.551 432.7

4/29/2010 12:49:35 6.486 12.346 15.695 254.79

Begin calculating run averages

4/29/2010 12:51:03 6.468 12.378 14.492 237.16

4/29/2010 12:52:03 6.557 12.301 14.456 235.86

4/29/2010 12:53:03 6.465 12.372 16.012 234.87

4/29/2010 12:54:03 6.433 12.385 16.92 235.48

4/29/2010 12:55:03 6.588 12.256 14.961 235.8

4/29/2010 12:56:03 6.546 12.272 15.279 234.33

4/29/2010 12:57:03 6.388 12.352 14.695 232.58

4/29/2010 12:58:03 6.529 12.236 13.623 231.56

4/29/2010 12:59:04 6.643 12.183 12.95 230.35

4/29/2010 13:00:04 6.583 12.239 13.54 228.19

4/29/2010 13:01:04 6.681 12.17 13.764 226.68

4/29/2010 13:02:04 6.581 12.258 12.338 225.61

4/29/2010 13:03:04 6.556 12.266 10.508 225.4

4/29/2010 13:04:04 6.669 12.169 12.815 225.4

4/29/2010 13:05:04 6.739 12.125 12.522 226.36

4/29/2010 13:06:04 6.634 12.205 11.723 225.88

4/29/2010 13:07:04 6.577 12.246 12.828 225.85

4/29/2010 13:08:04 6.627 12.213 12.667 225.39

4/29/2010 13:09:04 6.686 12.148 12.365 224.88

4/29/2010 13:10:04 6.601 12.209 12.821 225.73

4/29/2010 13:11:04 6.509 12.286 12.673 226.74

4/29/2010 13:12:04 6.592 12.217 11.786 226.56

4/29/2010 13:13:04 6.533 12.257 10.228 225.32

4/29/2010 13:14:04 6.485 12.285 10.336 223.8

4/29/2010 13:15:04 6.656 12.145 11.846 222.68

4/29/2010 13:16:04 6.735 12.109 11.469 221.28

4/29/2010 13:17:04 6.472 12.315 11.065 221.09

4/29/2010 13:18:04 6.548 12.257 11.141 223.12

4/29/2010 13:19:04 6.625 12.205 11.028 221.51

4/29/2010 13:20:04 6.478 12.312 10.135 220.21

4/29/2010 13:21:04 6.422 12.301 10.647 220.23

4/29/2010 13:22:04 6.601 12.194 12.44 220.57

4/29/2010 13:23:04 6.599 12.216 11.178 220.13

4/29/2010 13:24:04 6.492 12.286 10.376 220.66

4/29/2010 13:25:04 6.449 12.307 14.106 221.89

4/29/2010 13:26:04 6.677 12.135 11.943 222.18

4/29/2010 13:27:04 6.676 12.15 9.396 221.32

4/29/2010 13:28:04 6.375 12.361 9.261 224.2

4/29/2010 13:29:04 6.423 12.325 8.947 226.12

4/29/2010 13:30:04 6.748 12.074 9.384 224.8

4/29/2010 13:31:04 6.644 12.153 9.62 223.86

4/29/2010 13:32:04 6.487 12.264 10.079 225.26

# 4/29/2010 13:33:04 6.622 12.176 10.761 224.96

4/29/2010 13:34:04 6.503 12.278 10.604 224.45

4/29/2010 13:35:04 6.506 12.26 11.174 224.44

4/29/2010 13:36:04 6.668 12.137 12.027 224.47

4/29/2010 13:37:04 6.744 12.08 14.894 222.61

4/29/2010 13:38:04 6.684 12.147 13.19 222.95

4/29/2010 13:39:04 6.571 12.223 11.654 222.35

4/29/2010 13:40:04 6.484 12.277 11.282 222.91

4/29/2010 13:41:05 6.624 12.18 10.311 223.56

4/29/2010 13:42:05 6.608 12.19 10.061 222.71

4/29/2010 13:43:05 6.43 12.322 9.524 222.17

4/29/2010 13:44:05 6.394 12.355 9.018 222.39

4/29/2010 13:45:05 6.715 12.111 9.125 222.78

4/29/2010 13:46:05 6.606 12.197 11.813 221.24

4/29/2010 13:47:05 6.544 12.239 11.814 222.63

4/29/2010 13:48:05 6.66 12.159 10.884 222.44

4/29/2010 13:49:05 6.534 12.247 10.609 223.09

4/29/2010 13:50:05 6.461 12.313 10.827 225.25

4/29/2010 13:51:05 6.542 12.259 11.717 225.88

4/29/2010 13:52:05 6.613 12.206 11.376 224.57

4/29/2010 13:53:05 6.66 12.173 12.387 223.7

4/29/2010 13:54:05 6.47 12.33 13.31 224.17

4/29/2010 13:55:05 6.69 12.159 12.818 225.84

4/29/2010 13:56:05 6.678 12.169 12.455 224.61

4/29/2010 13:57:05 6.419 12.355 14.168 225.84

4/29/2010 13:58:05 6.66 12.174 13.785 227.07

4/29/2010 13:59:05 6.746 12.118 13.878 225.97

4/29/2010 14:00:05 6.496 12.307 15.267 226.79

4/29/2010 14:01:05 6.591 12.231 14.503 227.49

4/29/2010 14:02:05 6.62 12.227 13.785 227.3

4/29/2010 14:03:05 6.553 12.271 13.924 229.92

4/29/2010 14:04:05 6.739 12.116 17.598 232.2

4/29/2010 14:05:05 6.642 12.203 14.993 231.81

4/29/2010 14:06:05 6.562 12.263 14.253 232.97

4/29/2010 14:07:05 6.593 12.222 15.81 232.38

4/29/2010 14:08:05 6.839 12.039 15.632 231.38

4/29/2010 14:09:05 6.747 12.114 14.472 229.9

4/29/2010 14:10:05 6.673 12.165 13.182 229.6

4/29/2010 14:11:05 6.566 12.239 12.451 229.01

4/29/2010 14:12:05 6.599 12.213 11.41 227.93

4/29/2010 14:13:05 6.603 12.216 11.169 226.93

4/29/2010 14:14:05 6.616 12.21 11.154 227.19

4/29/2010 14:15:05 6.549 12.266 10.796 227.69

4/29/2010 14:16:05 6.498 12.313 11.584 227.49

4/29/2010 14:17:05 6.888 11.995 11.844 226.28

4/29/2010 14:18:05 6.831 12.029 12.677 224.14

4/29/2010 14:19:05 6.563 12.231 13.987 225.48

4/29/2010 14:20:05 6.619 12.189 13.816 227.5

4/29/2010 14:21:05 6.806 12.036 12.206 227.59

4/29/2010 14:22:05 6.643 12.15 12.079 227.36

4/29/2010 14:23:05 6.489 12.266 12.951 228.32

# 4/29/2010 14:24:05 6.697 12.107 13.271 228.57

4/29/2010 14:25:05 6.971 11.9 12.11 227.06

4/29/2010 14:26:05 6.62 12.158 13.494 226.89

4/29/2010 14:27:03 6.379 12.334 13.858 228.76

4/29/2010 14:28:03 6.846 11.963 17.876 228

4/29/2010 14:29:03 7.006 11.847 17.869 226.44

4/29/2010 14:30:03 6.491 12.247 16.88 226.87

4/29/2010 14:31:03 6.453 12.273 17.456 229.29

4/29/2010 14:32:03 6.782 12.022 15.994 228.38

4/29/2010 14:33:03 6.768 12.025 15.147 227.09

4/29/2010 14:34:03 6.608 12.144 14.439 226.9

4/29/2010 14:35:03 6.612 12.147 13.317 227.46

4/29/2010 14:36:04 6.73 12.061 12.696 227.31

4/29/2010 14:37:04 6.618 12.154 11.417 227.25

4/29/2010 14:38:04 6.603 12.156 11.257 229.1

4/29/2010 14:39:04 6.828 11.988 12.877 227.12

4/29/2010 14:40:04 6.877 11.945 11.801 225.39

4/29/2010 14:41:04 6.574 12.168 11.824 225.52

4/29/2010 14:42:04 6.464 12.256 11.779 225.93

4/29/2010 14:43:04 6.821 11.974 11.648 223.98

4/29/2010 14:44:04 6.718 12.059 15.175 222.7

4/29/2010 14:45:04 6.64 12.123 13.513 224.05

4/29/2010 14:46:04 6.724 12.058 12.693 224.09

4/29/2010 14:47:04 6.646 12.123 11.54 223.73

4/29/2010 14:48:04 6.703 12.088 10.87 224.43

4/29/2010 14:49:04 6.668 12.132 11.606 223.98

4/29/2010 14:50:04 6.789 12.036 11.26 224.06

4/29/2010 14:51:04 6.549 12.215 10.806 224.74

4/29/2010 14:52:04 6.733 12.085 11.51 226.62

4/29/2010 14:53:04 6.83 12.03 10.667 225.17

4/29/2010 14:54:04 6.726 12.102 10.283 226.08

4/29/2010 14:55:04 6.559 12.223 10.803 227.7

4/29/2010 14:56:04 6.773 12.058 10.451 229.41

4/29/2010 14:57:04 6.677 12.141 9.883 228.33

4/29/2010 14:58:04 6.575 12.205 10.244 228.26

4/29/2010 14:59:04 6.65 12.132 14.673 227.22

4/29/2010 15:00:04 6.675 12.13 12.815 225.85

4/29/2010 15:01:04 6.817 12.025 11.165 226.05

4/29/2010 15:02:04 6.612 12.182 10.161 225.87

4/29/2010 15:03:04 6.735 12.079 9.229 225.27

4/29/2010 15:04:04 6.758 12.062 9.634 223.64

4/29/2010 15:05:04 6.501 12.26 9.452 224.82

4/29/2010 15:06:04 6.585 12.202 9.068 226.03

4/29/2010 15:07:04 6.729 12.106 8.598 225.32

4/29/2010 15:08:04 6.671 12.143 8.406 224.44

4/29/2010 15:09:05 6.684 12.125 7.857 224.41

4/29/2010 15:10:05 6.499 12.258 8.939 222.82

4/29/2010 15:11:05 6.597 12.198 10.447 222.21

4/29/2010 15:12:05 6.844 12.014 9.503 221.24

4/29/2010 15:13:05 6.712 12.12 10.948 221.55

4/29/2010 15:14:05 6.664 12.163 9.625 222.3

# 4/29/2010 15:15:05 6.734 12.113 8.857 223.16

4/29/2010 15:16:05 6.783 12.161 8.521 223.76

4/29/2010 15:17:05 6.802 12.161 7.791 223.26

4/29/2010 15:18:05 6.619 12.292 7.949 222.71

4/29/2010 15:19:05 6.476 12.403 8.601 223.95

4/29/2010 15:20:05 6.562 12.325 7.643 223.6

4/29/2010 15:21:05 6.822 12.12 9.082 221.49

4/29/2010 15:22:05 6.644 12.269 9.108 221.69

4/29/2010 15:23:05 6.529 12.354 7.906 222.42

4/29/2010 15:24:05 6.544 12.355 7.095 223.25

4/29/2010 15:25:05 6.711 12.228 6.594 224.17

4/29/2010 15:26:05 6.673 12.252 6.061 223.92

4/29/2010 15:27:05 6.391 12.457 6.27 224.6

4/29/2010 15:28:05 6.727 12.178 9.737 224.84

4/29/2010 15:29:05 6.698 12.214 9.868 222.52

4/29/2010 15:30:05 6.511 12.356 9.261 222.89

4/29/2010 15:31:05 6.656 12.231 10.831 223.69

4/29/2010 15:32:05 6.767 12.13 12.478 221.55

4/29/2010 15:33:05 6.81 12.105 10.412 220.64

4/29/2010 15:34:05 6.601 12.268 9.7 222.09

4/29/2010 15:35:05 6.505 12.332 8.884 223.73

4/29/2010 15:36:05 6.637 12.238 8.62 222.95

4/29/2010 15:37:05 6.517 12.333 8.183 222.26

4/29/2010 15:38:05 6.442 12.402 7.761 222.1

4/29/2010 15:39:05 6.562 12.297 8.675 222.04

4/29/2010 15:40:05 6.595 12.283 12.376 221.72

4/29/2010 15:41:05 6.447 12.395 9.56 222.66

4/29/2010 15:42:05 6.36 12.452 10.448 222.04

4/29/2010 15:43:05 6.638 12.264 11.178 220.71

4/29/2010 15:44:05 6.638 12.272 10.029 219.48

4/29/2010 15:45:05 6.474 12.387 10.187 220.02

4/29/2010 15:46:05 6.587 12.302 10.056 219.3

4/29/2010 15:47:05 6.618 12.276 9.488 217.53

4/29/2010 15:48:05 6.593 12.286 9.052 216.7

4/29/2010 15:49:05 6.469 12.373 9.032 216.97

4/29/2010 15:50:05 6.448 12.396 8.241 217.74

Average of Test Run O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 15:50:05 6.618 12.203 11.565 225.17

Test Run 2 End

# Final System Bias Check for Run 2 . STRATA Version 3.2

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 15:51:32 4.606 4.987 7.069 191.73

4/29/2010 15:52:32 0.13 0.035 2.29 0.44

4/29/2010 15:53:32 7.19 7.162 1.736 -0.4

4/29/2010 15:54:32 9.586 9.475 1.244 -0.64

4/29/2010 15:55:32 0.209 0.106 23.579 -0.64

4/29/2010 15:56:32 0.122 0.008 39.256 -0.64

4/29/2010 15:57:32 0.114 -0.008 41.653 -0.64

4/29/2010 15:58:32 0.118 0.886 42.377 -0.76

4/29/2010 15:59:32 0.101 10.765 14.359 285.22

4/29/2010 16:00:32 0.099 10.836 3.325 440.84

Final System Bias Check for Run 2

Operator: M. Martin

Plant Nam e Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

NOx CC281576 SG9154467

Date/Time 4/29/2010 16:00:40 PASSED

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref C 0000

Zero Cal 0.044 0.034 -0.14 0.18

Zero Avg 0.128 0.028 2.039 0.07

Zero Bias % 0.4 0 2.4 0

Zero Drift % 0.1 -0.2 0.7 -0.2

Span Ref C 9.993 10 45.2 449.2

Span Cal 9.955 9.996 45.473 452.08

Span Avg 9.865 9.837 42.29 440.02

Span Bias % 0.4 0.9 3.5 2.7

Span Drift % 0.1 -0.4 -0.7 -0.6

Ini Zero Av 0.099 0.062 1.417 0.77

Ini Span A v 9.844 9.908 42.965 442.6

Run Avg 6.618 12.203 11.565 225.17

Co 0.114 0.045 1.728 0.42

Cm 9.855 9.872 42.628 441.31

Correct Av g 6.673 12.371 10.871 228.98

# Test Run 3 Begin. STRATA Version 3.2

Operator: M. Martin

Plant Nam e Dominion Southampton

Location: Common Stack

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 16:01:40 3.246 11.694 6.139 421.26

4/29/2010 16:02:40 6.264 12.516 12.537 230.54

4/29/2010 16:03:40 6.251 12.541 13.376 224.56

4/29/2010 16:04:41 6.55 12.337 12.752 220.32

4/29/2010 16:05:41 6.308 12.524 11.877 219.32

Begin calculating run averages

4/29/2010 16:07:05 6.388 12.462 12.081 220.52

4/29/2010 16:08:03 6.513 12.362 11.429 218.94

4/29/2010 16:09:03 6.379 12.47 11.286 218.81

4/29/2010 16:10:03 6.284 12.546 11.056 220.46

4/29/2010 16:11:03 6.295 12.536 11.474 221.87

4/29/2010 16:12:03 6.331 12.517 10.728 222.45

4/29/2010 16:13:03 6.371 12.474 9.888 222.35

4/29/2010 16:14:03 6.408 12.439 13.194 222.52

4/29/2010 16:15:03 6.265 12.585 13.588 222.42

4/29/2010 16:16:03 6.429 12.465 12.551 223.53

4/29/2010 16:17:03 6.539 12.373 14.02 223.61

4/29/2010 16:18:03 6.459 12.439 11.268 224.24

4/29/2010 16:19:03 6.364 12.501 10.72 223.86

4/29/2010 16:20:03 6.34 12.512 10.923 225.11

4/29/2010 16:21:03 6.421 12.448 9.833 225.01

4/29/2010 16:22:03 6.282 12.565 9.751 224.74

4/29/2010 16:23:03 6.322 12.534 9.254 226.59

4/29/2010 16:24:03 6.529 12.355 9.851 225.39

4/29/2010 16:25:03 6.423 12.448 11.274 225.29

4/29/2010 16:26:03 6.32 12.532 11.3 227.19

4/29/2010 16:27:03 6.367 12.499 10.449 227.62

4/29/2010 16:28:03 6.485 12.412 10.55 227.39

4/29/2010 16:29:03 6.349 12.525 10.838 226.71

4/29/2010 16:30:03 6.256 12.592 11.709 228.33

4/29/2010 16:31:03 6.338 12.539 11.584 230.05

4/29/2010 16:32:03 6.579 12.344 11.892 228.99

4/29/2010 16:33:03 6.335 12.546 13.826 228.12

4/29/2010 16:34:04 6.383 12.499 11.733 231.25

4/29/2010 16:35:04 6.612 12.315 15.465 231.17

4/29/2010 16:36:04 6.503 12.406 13.358 230.16

4/29/2010 16:37:04 6.527 12.384 12.507 230.87

4/29/2010 16:38:04 6.442 12.447 12.103 229.63

4/29/2010 16:39:04 6.464 12.432 11.489 229.17

4/29/2010 16:40:04 6.497 12.41 11.414 228.59

4/29/2010 16:41:04 6.446 12.448 11.348 227.98

4/29/2010 16:42:04 6.371 12.504 12.663 227.57

4/29/2010 16:43:04 6.393 12.503 13.757 226.51

4/29/2010 16:44:04 6.405 12.502 11.9 226.63

4/29/2010 16:45:04 6.562 12.36 13.58 224.93

# 4/29/2010 16:46:04 6.371 12.513 15.303 225.08

4/29/2010 16:47:04 6.455 12.459 14.147 226

4/29/2010 16:48:04 6.425 12.477 13.606 227.51

4/29/2010 16:49:04 6.514 12.401 13.147 228.71

4/29/2010 16:50:04 6.347 12.532 13.735 229.23

4/29/2010 16:51:04 6.597 12.335 13.417 230.57

4/29/2010 16:52:04 6.513 12.401 13.46 229.48

4/29/2010 16:53:04 6.389 12.48 14.317 231.59

4/29/2010 16:54:04 6.559 12.359 13.201 230.97

4/29/2010 16:55:04 6.444 12.432 12.057 231.04

4/29/2010 16:56:04 6.403 12.469 13.875 231.1

4/29/2010 16:57:04 6.469 12.412 12.773 231.59

4/29/2010 16:58:04 6.517 12.373 11.382 231.01

4/29/2010 16:59:04 6.392 12.472 10.641 231.38

4/29/2010 17:00:04 6.44 12.415 14.92 231.85

4/29/2010 17:01:04 6.55 12.344 15.305 229.62

4/29/2010 17:02:04 6.385 12.466 14.29 229.01

4/29/2010 17:03:04 6.487 12.381 14.197 228.45

4/29/2010 17:04:04 6.526 12.34 14.004 226.51

4/29/2010 17:05:04 6.585 12.279 14.127 226.04

4/29/2010 17:06:04 6.38 12.433 15.883 226.05

4/29/2010 17:07:04 6.372 12.434 16.136 226.31

4/29/2010 17:08:04 6.411 12.427 13.826 223.96

4/29/2010 17:09:04 6.634 12.242 15.385 223.78

4/29/2010 17:10:04 6.484 12.352 17.88 223.45

4/29/2010 17:11:04 6.371 12.439 15.585 224.07

4/29/2010 17:12:04 6.498 12.348 15.257 223.93

4/29/2010 17:13:04 6.543 12.319 15.155 223.19

4/29/2010 17:14:04 6.469 12.359 16.372 223.44

4/29/2010 17:15:04 6.374 12.437 15.909 223.39

4/29/2010 17:16:04 6.589 12.27 14.149 224.33

4/29/2010 17:17:04 6.602 12.25 14.979 223.88

4/29/2010 17:18:04 6.48 12.339 14.211 224.12

4/29/2010 17:19:04 6.368 12.424 13.765 224.44

4/29/2010 17:20:04 6.544 12.29 13.821 225.05

4/29/2010 17:21:05 6.603 12.255 13.229 224.83

4/29/2010 17:22:05 6.502 12.321 12.409 225.74

4/29/2010 17:23:05 6.453 12.36 14.39 226.29

4/29/2010 17:24:03 6.591 12.255 13.75 226.35

4/29/2010 17:25:03 6.42 12.393 13.151 225.37

4/29/2010 17:26:03 6.367 12.443 13.247 226.36

4/29/2010 17:27:03 6.534 12.305 13.696 226.03

4/29/2010 17:28:03 6.621 12.236 15.047 224.9

4/29/2010 17:29:03 6.542 12.305 12.259 224.53

4/29/2010 17:30:03 6.553 12.298 10.163 225.29

4/29/2010 17:31:03 6.423 12.398 9.823 226.67

4/29/2010 17:32:03 6.506 12.336 10.589 227.54

4/29/2010 17:33:03 6.53 12.32 10.902 227.11

4/29/2010 17:34:03 6.428 12.398 10.988 225.53

4/29/2010 17:35:03 6.383 12.436 12.314 225.16

4/29/2010 17:36:03 6.479 12.372 13.127 224.19

# 4/29/2010 17:37:03 6.526 12.34 11.388 222.71

4/29/2010 17:38:03 6.538 12.306 15.425 221.42

4/29/2010 17:39:03 6.509 12.339 14.7 221.34

4/29/2010 17:40:03 6.522 12.334 12.714 221.45

4/29/2010 17:41:03 6.431 12.408 12.65 222.63

4/29/2010 17:42:03 6.485 12.371 13.107 223.51

4/29/2010 17:43:03 6.463 12.382 12.661 224.3

4/29/2010 17:44:03 6.526 12.336 12.28 223.71

4/29/2010 17:45:03 6.336 12.489 12.564 223.62

4/29/2010 17:46:03 6.328 12.487 13.306 225.33

4/29/2010 17:47:03 6.457 12.403 15.614 225.14

4/29/2010 17:48:03 6.461 12.389 13.761 224.49

4/29/2010 17:49:03 6.411 12.418 15.81 224.2

4/29/2010 17:50:03 6.473 12.377 15.763 223.9

4/29/2010 17:51:03 6.393 12.453 14.143 224.24

4/29/2010 17:52:03 6.55 12.336 12.574 224.51

4/29/2010 17:53:03 6.655 12.25 11.049 223.64

4/29/2010 17:54:03 6.234 12.568 11.658 223.76

4/29/2010 17:55:04 6.494 12.371 14.068 225.98

4/29/2010 17:56:04 6.683 12.229 13.656 225.19

4/29/2010 17:57:04 6.512 12.355 13.906 223.66

4/29/2010 17:58:04 6.345 12.478 14.001 224.34

4/29/2010 17:59:04 6.311 12.51 17.985 224.45

4/29/2010 18:00:04 6.372 12.47 18.865 223.11

4/29/2010 18:01:04 6.531 12.356 15.635 221.94

4/29/2010 18:02:04 6.385 12.452 20.149 221.08

4/29/2010 18:03:04 6.314 12.52 16.86 221.46

4/29/2010 18:04:04 6.519 12.379 14.628 221.01

4/29/2010 18:05:04 6.404 12.449 13.812 219.61

4/29/2010 18:06:04 6.329 12.511 12.996 220.47

4/29/2010 18:07:04 6.218 12.597 13.985 220.98

4/29/2010 18:08:04 6.393 12.473 14.045 221.96

4/29/2010 18:09:04 6.457 12.414 14.351 220.67

4/29/2010 18:10:04 6.364 12.46 15.146 220.42

4/29/2010 18:11:04 6.282 12.528 17.072 220.49

4/29/2010 18:12:04 6.376 12.493 17.64 219.68

4/29/2010 18:13:05 6.215 12.617 17.779 218.69

4/29/2010 18:14:05 6.293 12.547 15.285 219.18

4/29/2010 18:15:05 6.442 12.439 14.015 217.07

4/29/2010 18:16:05 6.353 12.525 14.248 217.31

4/29/2010 18:17:05 6.417 12.465 14.111 217.79

4/29/2010 18:18:05 6.208 12.622 13.971 218.54

4/29/2010 18:19:05 6.283 12.564 13.015 220.66

4/29/2010 18:20:05 6.438 12.43 14.88 219.75

4/29/2010 18:21:05 6.331 12.523 15.787 220.2

4/29/2010 18:22:05 6.503 12.395 16.47 222.31

4/29/2010 18:23:05 6.606 12.31 17.391 221.93

4/29/2010 18:24:05 6.379 12.471 16.278 221.66

4/29/2010 18:25:03 6.444 12.426 15.25 223.24

4/29/2010 18:26:03 6.523 12.364 20.613 224.39

4/29/2010 18:27:03 6.503 12.38 17.937 223.67

# 4/29/2010 18:28:03 6.469 12.409 16.106 223.87

4/29/2010 18:29:03 6.368 12.489 15.907 224.65

4/29/2010 18:30:03 6.524 12.356 15.675 223.93

4/29/2010 18:31:03 6.778 12.148 18.092 221.61

4/29/2010 18:32:03 6.505 12.364 17.498 220.55

4/29/2010 18:33:03 6.362 12.474 16.373 221.29

4/29/2010 18:34:03 6.595 12.314 16.002 221.08

4/29/2010 18:35:03 6.502 12.384 15.559 219.71

4/29/2010 18:36:03 6.563 12.33 14.191 219.29

4/29/2010 18:37:03 6.385 12.468 14.684 219.88

4/29/2010 18:38:03 6.459 12.41 14.125 220.22

4/29/2010 18:39:03 6.471 12.419 14.241 218.84

4/29/2010 18:40:03 6.188 12.633 14.807 220.58

4/29/2010 18:41:03 6.386 12.469 18.93 221.96

4/29/2010 18:42:03 6.65 12.296 17.311 221.3

4/29/2010 18:43:03 6.364 12.519 16.801 222.63

4/29/2010 18:44:03 6.453 12.447 17.982 225.35

4/29/2010 18:45:03 6.547 12.378 16.918 224.78

4/29/2010 18:46:03 6.512 12.395 17.412 224.2

4/29/2010 18:47:03 6.456 12.435 17.825 223.52

4/29/2010 18:48:03 6.366 12.51 18.669 223.55

4/29/2010 18:49:03 6.419 12.472 19.419 224.53

4/29/2010 18:50:03 6.611 12.34 18.883 224.21

4/29/2010 18:51:03 6.499 12.414 17.719 223.57

4/29/2010 18:52:03 6.483 12.415 21.142 224.51

4/29/2010 18:53:03 6.542 12.382 20.487 225.51

4/29/2010 18:54:03 6.436 12.47 18.006 226.44

4/29/2010 18:55:03 6.507 12.414 17.887 228.06

4/29/2010 18:56:03 6.344 12.546 17.663 228.66

4/29/2010 18:57:03 6.403 12.498 16.12 231.07

4/29/2010 18:58:03 6.712 12.254 19.768 230.52

4/29/2010 18:59:03 6.596 12.356 18.135 230.3

4/29/2010 19:00:03 6.476 12.443 16.808 231.19

4/29/2010 19:01:03 6.393 12.492 17.472 231.3

4/29/2010 19:02:04 6.492 12.428 17.564 230.2

4/29/2010 19:03:04 6.71 12.268 16.063 230.12

4/29/2010 19:04:04 6.454 12.474 16.359 228.84

4/29/2010 19:05:04 6.309 12.588 17.531 230.7

4/29/2010 19:06:04 6.79 12.213 17.668 230.37

Average of Test Run O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 19:06:04 6.45 12.42 14.354 224.82

Test Run 3 End

# Final System Bias Check for Run 3 . STRATA Version 3.2

O2 CO2 SO2 NOx

% % ppm ppm

4/29/2010 19:07:38 3.409 6.004 13.257 217.78

4/29/2010 19:08:38 0.123 0.11 3.375 14.54

4/29/2010 19:09:38 0.113 0.079 2.118 1.77

4/29/2010 19:10:38 0.107 0.069 1.72 1.37

4/29/2010 19:11:38 4.108 4.129 1.574 1.07

4/29/2010 19:12:38 9.843 9.893 1.532 0.8

4/29/2010 19:13:38 9.861 9.926 1.435 0.56

4/29/2010 19:14:38 9.868 9.937 1.431 0.47

4/29/2010 19:15:37 7.722 7.789 1.821 0.43

4/29/2010 19:16:37 0.15 0.151 30.037 0.94

4/29/2010 19:17:37 0.121 0.093 40.622 0.61

4/29/2010 19:18:37 0.115 0.077 42.47 0.17

4/29/2010 19:19:37 0.109 7.407 29.396 92.29

Final System Bias Check for Run 3

Operator: M. Martin

Plant Name: Dominion Southampton

Location: Common Stack

Reference Cylinder Numbers

Zero Span

O2 CC281576 SG9135786

CO2 CC281576 SG9135786

SO2 CC281576 CC308434

NOx CC281576 SG9154467

Date/Time 4/29/2010 19:20:31 PASSED

Analyte O2 CO2 SO2 NOx

Units % % ppm ppm

Zero Ref Cyl 0000

Zero Cal 0.044 0.034 -0.14 0.18

Zero Avg 0.112 0.065 1.709 1.07

Zero Bias% 0.3 0.2 2 0.2

Zero Drift% -0.1 0.2 -0.4 0.2

Span Ref Cyl 9.993 10 45.2 449.2

Span Cal 9.955 9.996 45.473 452.08

Span Avg 9.872 9.943 42.769 435.01

Span Bias% 0.4 0.3 3 3.8

Span Drift% 0 0.6 0.5 -1.1

Ini Zero Avg 0.128 0.028 2.039 0.07

Ini Span Avg 9.865 9.837 42.29 440.02

Run Avg 6.45 12.42 14.354 224.82

Co 0.12 0.046 1.874 0.57

Cm 9.868 9.89 42.529 437.52

Correct Avg 6.489 12.57 13.876 230.54

# L2010-275 

# APPENDIX A.7

VOLATILE ORGANIC FIELD SAMPLING DATA

# L2010-275 

# APPENDIX A.8

SEMI-VOLATILE ORGANICS FIELD DATA

# TEST DATA SUMMARY

Client: Dominion

Location: Southampton

Unit: Common Stack

Load/Condition: Normal

M0010 Dates: 4/28/2010

Prelim. Run 1 Run 2 Run 3

Dates: 4/28/2010 4/28/2010 4/28/2010

Barometric Pressures: 29.85 29.85 29.85



# TABLE OF CONTENTS:

K-Factor Sheet - Run 1

K-Factor Sheet - Run 2

K-Factor Sheet - Run 3

Nozzles

Data Sheet

Run Sheet - Preliminaries

Run Sheet - Run 1

Run Sheet - Run 2

Run Sheet - Run 3

Calculation Sheet

Parameter Run 1 Run 2 Run 3 3-RUN AVG.

Total Sampling Time, Min. 120 120 120 120

Stack Gas Oxygen Content, O2% 6.535 6.488 6.496 6.506

Stack Gas Carbon Dioxide Content, CO2% 12.605 12.643 12.635 12.628

Gas Sample Volume at Standard Conditions, cu. ft. 114.876 116.556 116.785 116.072

cu. m. 3.252 3.300 3.306 3.286

Dry Stack Gas Flow Rate (Dry, STP), dscf/min 194,969.5 192,598.1 190,870.2 192,812.6

dscm/min 5,519.6 5,452.5 5,403.5 5,458.5



# TRC Environmental Corporation

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

Project Number 170096-0030 Sampling Data Summary

M0010-South-U2 Runs 1-3.xlsTOC

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M0010

Common Stack

Normal

Run No: Run 1

Date: 4/28/2010

METER BOX ID: 90596 Orifice Delta H@: 1.830 Y FACTOR: 0.9965

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 5.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.25 in. Hg

% H 2 

# 0 Assumed Moisture Content 13.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter DCIR-7/32"-3 0.218 inches

Delta H@ Orifice Calibration Factor 1.830 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -0.4 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 29.00 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 28.97 in. Hg

Md Dry Molecular Weight 30.12 lb/lb*mole

Ms Wet Molecular Weight 28.54 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 70 80 90 100

200 1.58 1.61 1.64 1.67

205 1.57 1.60 1.63 1.66

210 1.56 1.59 1.62 1.65

215 1.55 1.58 1.61 1.63

220 1.54 1.56 1.59 1.62

225 1.52 1.55 1.58 1.61

230 1.51 1.54 1.57 1.60

235 1.50 1.53 1.56 1.59

240 1.49 1.52 1.55 1.58

245 1.48 1.51 1.54 1.56

250 1.47 1.50 1.53 1.55

255 1.46 1.49 1.52 1.54

260 1.45 1.48 1.51 1.53

265 1.44 1.47 1.49 1.52

270 1.43 1.46 1.48 1.51

275 1.42 1.45 1.47 1.50

280 1.41 1.44 1.46 1.49

285 1.40 1.43 1.45 1.48

290 1.39 1.42 1.44 1.47

295 1.38 1.41 1.44 1.46

300 1.37 1.40 1.43 1.45

305 1.36 1.39 1.42 1.44

310 1.36 1.38 1.41 1.43

315 1.35 1.37 1.40 1.42

320 1.34 1.36 1.39 1.41

321 1.34 1.36 1.39 1.41

Delta H = K factor * Delta P 

# M0010

M0010-South-U2 Runs 1-3.xls K-Fs R1 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M0010

Common Stack

Normal

Run No: Run 2

Date: 4/28/2010

METER BOX ID: 90596 Orifice Delta H@: 1.830 Y FACTOR: 0.997

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.85 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.830 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 29.60 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 29.45 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 60 70 80 90

250 1.57 1.60 1.63 1.66

255 1.56 1.59 1.62 1.65

260 1.55 1.58 1.61 1.64

265 1.54 1.57 1.60 1.63

270 1.53 1.56 1.59 1.62

275 1.52 1.55 1.58 1.61

280 1.51 1.54 1.57 1.60

285 1.50 1.53 1.56 1.59

290 1.49 1.52 1.55 1.58

295 1.48 1.51 1.54 1.57

300 1.47 1.50 1.53 1.56

305 1.46 1.49 1.52 1.55

310 1.45 1.48 1.51 1.54

315 1.44 1.47 1.50 1.53

320 1.43 1.46 1.49 1.52

325 1.42 1.45 1.48 1.51

330 1.41 1.44 1.47 1.50

335 1.41 1.43 1.46 1.49

340 1.40 1.42 1.45 1.48

345 1.39 1.41 1.44 1.47

350 1.38 1.41 1.43 1.46

355 1.37 1.40 1.42 1.45

360 1.36 1.39 1.42 1.44

365 1.35 1.38 1.41 1.43

370 1.35 1.37 1.40 1.42

375 1.34 1.36 1.39 1.42

Delta H = K factor * Delta P 

# M0010

M0010-South-U2 Runs 1-3.xls K-Fs R2 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M0010

Common Stack

Normal

Run No: Run 3

Date: 4/28/2010

METER BOX ID: 90596 Orifice Delta H@: 1.830 Y FACTOR: 0.997

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.85 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.830 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 29.60 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 29.45 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 55 65 75 85

270 1.52 1.55 1.58 1.60

275 1.51 1.54 1.56 1.59

280 1.50 1.52 1.55 1.58

285 1.49 1.51 1.54 1.57

290 1.48 1.50 1.53 1.56

295 1.47 1.49 1.52 1.55

300 1.46 1.48 1.51 1.54

305 1.45 1.47 1.50 1.53

310 1.44 1.47 1.49 1.52

315 1.43 1.46 1.48 1.51

320 1.42 1.45 1.47 1.50

325 1.41 1.44 1.46 1.49

330 1.40 1.43 1.46 1.48

335 1.39 1.42 1.45 1.47

340 1.38 1.41 1.44 1.46

345 1.37 1.40 1.43 1.45

350 1.37 1.39 1.42 1.45

355 1.36 1.38 1.41 1.44

360 1.35 1.38 1.40 1.43

365 1.34 1.37 1.39 1.42

370 1.33 1.36 1.39 1.41

375 1.33 1.35 1.38 1.40

380 1.32 1.34 1.37 1.39

385 1.31 1.34 1.36 1.39

390 1.30 1.33 1.35 1.38

395 1.29 1.32 1.34 1.37

Delta H = K factor * Delta P 

# M0010

M0010-South-U2 Runs 1-3.xls K-Fs R3 

# TRC Environmental Corporation

# NOZZLE SELECTION CALCULATIONS 

# M0010

Common Stack

Normal

CHECK ALL INPUTS

Hand Input or Check Links

Input By:

Run 1 Run 2 Run 3

Date: 4/28/2010 4/28/2010 4/28/2010

Bar. Pressure, Pbar, in. Hg 29.85 29.85 29.85

Stack Temp.(F), ts (from prev. run) 125.0 191.9 191.9

Stack Temp. (R), Ts 585 652 652

Meter Temp. (F), tm 70.0 74.4 90.0

Meter Temp. (R), Tm 530 534 550

Pitot Number 0.0 0.0 0.0

Pitot Coefficient, cp 0.84 0.84 0.84

delta P avg. (from prev. run), dP, in. H2O 

# 0.94 2.01 2.09

O2 avg. (from prev. run), % 5.50 6.54 6.49

CO2 avg. (from prev. run), % 12.00 12.61 12.64

Static Pressure (from prev. run), in. H2O 

# -0.40 -0.96 -0.89

Ps, in. Hg 29.821 29.779 29.785

Mwd, lb/lb mole, dry 30.14 30.28 30.28

% Moisture (from prev. run) 13.0 8.9 12.5

MD 0.870 0.911 0.875

Mws, lb/lb mole, wet 28.562 29.185 28.751

delta H, (for sampling rate), in. H2O 1.830 1.830 1.830

delta H@, in. H2O 1.830 1.830 1.830

Qm, dscfm 0.750 0.750 0.750

Desired Nozzle , inches 0.224 0.187 0.185



# For Standard Test: dH = dH@, and therefore, Qm will be 0.75 dscfm.

For Different Sampling Rate: Input selected dH to yield desired sampling rate.

Desired Nozzle:

SQRT(SQRT((Ts*Mws)/(Ps*dP))*(0.0357*Qm*Pbar)/(Tm*cp*MD)) M0010

M0010-South-U2 Runs 1-3.xlsNozzles 

# TRC Environmental Corporation

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: #REF!

LOCATION: Southampton PROJECT NO.: 170096-0030

UNIT: Common Stack PERSONNEL: TRC

CONDITION: Normal



# Data Input Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.



# M0010

Parameter SYMBOL UNITS DATA Data

Test Number Prelim. Run 1 Run 2 Run 3

Test Date 1/0/1900 4/28/2010 4/28/2010 4/28/2010

Start Time 09:45 12:45 15:40

Stop Time 11:51 14:55 17:53 3-RUN AVG.

Stack Diameter ds inches 318.00 96.00 96.00 96.00

Nozzle Diameter dn inches 0.218 0.218 0.218

Barometric Pressure Pbar in. Hg 29.85 29.85 29.85 29.85

Stack Static Pressure Pg in. H2O -0.96 -0.89 -1.00 -0.95

Pitot Coefficient cp none 0.84 0.84 0.84 0.84

Meter Calibration Factor Y none 0.9965 0.9965 0.9965

DH@ none 1.8300 1.8300 1.8300

Stack Gas Oxygen Content O2 % 6.535 6.488 6.496 6.506

Stack Gas Carbon Dioxide Content CO2 % 12.605 12.643 12.635 12.628

Net Moisture Gain (Impingers w/SiGel) Ww grams 238.1 352.0 350.9 313.7

Average Stack Temperature ts deg F 191.9 191.9 190.3 191.4

Average Meter Temperature tm deg F 58.4 64.9 66.8 63.4

Avg Delta H dH in. H2O 3.24 3.33 3.25 3.28

Average Square Root Delta H ASR dH in. H2O 1.799 1.825 1.801 1.808

Avg Velocity Head dP in. H2O 2.01 2.09 2.05 2.05

Average Square Root Delta P ASR dP in H2O 1.415 1.444 1.429 1.429

Gas Sample Volume Vm cu. ft. 112.558 115.610 116.261 114.810

Total Sampling Time min minutes 120 120 120

M0010-South-U2 Runs 1-3.xls/Data 6/18/2010 8:58 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 28-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Common Stack

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 1 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

1 0 580.475 2.00 1.414 3.2 1.789 193 54 54

2 5 2.10 1.449 3.4 1.844 193 55 54

3 1 0 2.20 1.483 3.5 1.871 193 56 54

4 1 5 2.10 1.449 3.4 1.844 193 57 55

5 2 0 2.15 1.466 3.4 1.844 193 58 55

6 2 5 2.15 1.466 3.4 1.844 192 58 55

7 3 0 1.25 1.118 2.5 1.581 192 58 55

8 3 5 2.15 1.466 3.4 1.844 192 58 56

9 4 0 2.15 1.466 3.4 1.844 192 58 56

10 45 2.00 1.414 3.2 1.789 192 58 56

11 50 1.85 1.360 3.0 1.732 192 58 57

12 55 1.70 1.304 2.7 1.643 191 59 57

13 60 635.299

635.299 1.83 1.353 3.0 1.732 187 57 57

14 65 2.05 1.432 3.3 1.817 191 60 57

15 70 2.05 1.432 3.3 1.817 191 60 58

16 75 2.10 1.449 3.4 1.844 191 63 58

17 80 2.10 1.449 3.4 1.844 192 62 58

18 85 2.10 1.449 3.4 1.844 192 63 58

19 90 2.15 1.466 3.4 1.844 192 63 59

20 95 2.30 1.517 3.7 1.924 192 63 59

21 100 2.05 1.432 3.3 1.817 193 65 59

22 105 1.95 1.396 3.1 1.761 193 65 60

23 110 1.90 1.378 3.0 1.732 192 65 60

24 115 1.85 1.360 3.0 1.732 192 65 60

Stop 120 693.033

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

120.0 112.558 2.010 1.415 3.24 1.799 191.9 58.4

Impinger Gain

impinger 1: 769.0 569.0 200.0 O2: 6.535 Start Time: 09:45

impinger 1a: 541.7 540.0 1.7 CO2: 12.605 Stop Time: 11:51

impinger 2: 720.5 723.0 -2.5

impinger 3: 697.5 701.0 -3.5 Static Pressure (Port A): -0.96

impinger 4: 613.0 610.5 2.5 Static Pressure (Port B):

Si gel 1,028.5 992.0 36.5 Static Pressure (Avg.): -0.96

Trap 353.0 349.6 3.4

238.1 DIFF

PRESS. 

# M0010 

# Field Data Run Sheets

M0010-South-U2 Runs 1-3.xls/Run 1 6/18/2010 8:58 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 28-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Common Stack

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 2 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

1 0 693.306 1.70 1.304 2.7 1.643 190 61 60

2 5 1.75 1.323 2.8 1.673 191 62 61

3 10 2.00 1.414 3.2 1.789 191 64 61

4 15 2.05 1.432 3.3 1.817 191 64 61

5 20 2.15 1.466 3.4 1.844 191 65 61

6 25 2.10 1.449 3.4 1.844 191 65 61

7 30 2.05 1.432 3.3 1.817 191 65 61

8 35 2.10 1.449 3.4 1.844 191 65 61

9 40 2.15 1.466 3.4 1.844 191 66 62

10 45 2.15 1.466 3.4 1.844 191 67 62

11 50 2.15 1.466 3.4 1.844 192 68 63

12 55 2.00 1.414 3.2 1.789 193 67 63

13 60 750.175

750.861 2.15 1.466 3.4 1.844 193 64 63

14 65 2.25 1.500 3.6 1.897 193 67 64

15 70 2.15 1.466 3.4 1.844 193 67 64

16 75 2.20 1.483 3.5 1.871 193 66 64

17 80 2.25 1.500 3.6 1.897 193 68 64

18 85 2.20 1.483 3.5 1.871 193 71 65

19 90 2.10 1.449 3.4 1.844 193 71 65

20 95 2.15 1.466 3.4 1.844 194 70 66

21 100 2.15 1.466 3.4 1.844 194 68 66

22 105 2.05 1.432 3.3 1.817 193 69 65

23 110 2.05 1.432 3.3 1.817 189 71 65

24 115 2.05 1.432 3.3 1.817 190 72 66

Stop 120 809.602

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

120.0 115.610 2.088 1.444 3.33 1.825 191.9 64.9

Impinger Gain

impinger 1: 889.0 569.0 320.0 O2: 6.488 Start Time: 12:45

impinger 1a: 599.5 598.0 1.5 CO2: 12.643 Stop Time: 14:55

impinger 2: 722.0 724.5 -2.5

impinger 3: 736.5 737.5 -1.0 Static Pressure (Port A): -0.89

impinger 4: 636.5 634.5 2.0 Static Pressure (Port B): -0.89

Si gel 1024.0 995.0 29.0 Static Pressure (Avg.): -0.89

Trap 344.5 341.5 3.0

352.0 DIFF

PRESS. 

# M0010 

# Field Data Run Sheets

M0010-South-U2 Runs 1-3.xls/Run 2 6/18/2010 8:58 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 28-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Common Stack

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 3 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

1 0 809.853 1.5 1.225 2.4 1.549 190 63 65

2 5 2.2 1.466 3.4 1.844 190 66 65

3 10 2.2 1.483 3.5 1.871 190 68 65

4 15 2.2 1.483 3.5 1.871 190 69 65

5 20 2.2 1.483 3.5 1.871 190 70 66

6 25 2.2 1.483 3.5 1.871 190 69 66

7 30 2.2 1.466 3.4 1.844 190 70 6

8 35 2.2 1.466 3.4 1.844 190 72 67

9 40 2.2 1.466 3.4 1.844 190 72 67

10 45 2.0 1.414 3.2 1.789 190 72 67

11 50 2.0 1.396 3.1 1.761 191 71 68

12 55 2.0 1.396 3.1 1.761 191 71 67

13 60 867.961

868.134 2.0 1.396 3.0 1.732 190 66 66

14 65 2.0 1.414 3.2 1.789 191 69 66

15 70 2.1 1.449 3.4 1.844 191 69 66

16 75 2.2 1.466 3.4 1.844 191 70 66

17 80 2.3 1.500 3.5 1.871 191 70 66

18 85 2.2 1.466 3.4 1.844 190 72 66

19 90 2.2 1.466 3.4 1.844 190 72 66

20 95 2.1 1.449 3.4 1.844 191 71 66

21 100 2.1 1.432 3.3 1.817 191 70 67

22 105 2.0 1.396 3.1 1.761 190 71 67

23 110 1.8 1.342 2.9 1.703 190 71 67

24 115 1.7 1.285 2.6 1.612 189 70 67

Stop 120 926.287

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

120.0 116.261 2.046 1.429 3.25 1.801 190.3 66.8

Impinger Gain

impinger 1: 887.0 571.0 316.0 O2: 6.496 Start Time: 15:40

impinger 1a: 542.0 540.5 1.5 CO2: 12.635 Stop Time: 17:53

impinger 2: 718.5 721.8 -3.3

impinger 3: 699.0 701.5 -2.5 Static Pressure (Port A): -1.00

impinger 4: 612.5 611.0 1.5 Static Pressure (Port B): -1.00

Si gel 1037.0 1002.0 35.0 Static Pressure (Avg.): -1.00

Trap 347.2 344.5 2.7

350.9 DIFF

PRESS. 

# M0010 

# Field Data Run Sheets

M0010-South-U2 Runs 1-3.xls/Run 3 6/18/2010 8:58 PM

# L2010-275 

# APPENDIX A.9

FORMALDEHYDE FIELD SAMPLING DATA

# TEST DATA SUMMARY

Client: Dominion

Location: Southampton

Unit: Common Stack

Load/Condition: Normal

M0011 Dates:

Prelim. Run 1 Run 2 Run 3

Dates: 4/28/2010 4/28/2010 4/28/2010

Barometric Pressures: 29.85 29.85 29.85



# TABLE OF CONTENTS:

K-Factor Sheet - Run 1

K-Factor Sheet - Run 2

K-Factor Sheet - Run 3

Nozzles

Data Sheet

Run Sheet - Preliminaries

Run Sheet - Run 1

Run Sheet - Run 2

Run Sheet - Run 3

Calculation Sheet

Parameter Run 1 Run 2 Run 3 3-RUN AVG.

Total Sampling Time, Min. 120 120 120 120

Stack Gas Oxygen Content, O2% 6.535 6.488 6.496 6.506

Stack Gas Carbon Dioxide Content, CO2% 12.605 12.643 12.635 12.628

Gas Sample Volume at Standard Conditions, cu. ft. 115.172 112.663 114.636 114.157

cu. m. 3.261 3.189 3.245 3.232

Dry Stack Gas Flow Rate (Dry, STP), dscf/min 188,160.1 185,885.0 189,620.6 187,888.6

dscm/min 5,326.8 5,262.4 5,368.2 5,319.1



# TRC Environmental Corporation

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

Project Number 170096-0030 Sampling Data Summary

M0011-South-U2 Runs 1-3.xlsTOC

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M0011

Common Stack

Normal

Run No: Run 1

Date: 4/28/2010

METER BOX ID: 90801 Orifice Delta H@: 1.730 Y FACTOR: 0.9873

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 5.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.25 in. Hg

% H 2 

# 0 Assumed Moisture Content 13.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter DCIR-7/32"-4 0.218 inches

Delta H@ Orifice Calibration Factor 1.730 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -0.4 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 29.00 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 28.97 in. Hg

Md Dry Molecular Weight 30.12 lb/lb*mole

Ms Wet Molecular Weight 28.54 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 70 80 90 100

200 1.50 1.52 1.55 1.58

205 1.48 1.51 1.54 1.57

210 1.47 1.50 1.53 1.56

215 1.46 1.49 1.52 1.55

220 1.45 1.48 1.51 1.53

225 1.44 1.47 1.50 1.52

230 1.43 1.46 1.48 1.51

235 1.42 1.45 1.47 1.50

240 1.41 1.44 1.46 1.49

245 1.40 1.43 1.45 1.48

250 1.39 1.42 1.44 1.47

255 1.38 1.41 1.43 1.46

260 1.37 1.40 1.42 1.45

265 1.36 1.39 1.41 1.44

270 1.35 1.38 1.40 1.43

275 1.34 1.37 1.39 1.42

280 1.33 1.36 1.38 1.41

285 1.33 1.35 1.38 1.40

290 1.32 1.34 1.37 1.39

295 1.31 1.33 1.36 1.38

300 1.30 1.32 1.35 1.37

305 1.29 1.31 1.34 1.36

310 1.28 1.31 1.33 1.35

315 1.27 1.30 1.32 1.35

320 1.27 1.29 1.31 1.34

321 1.26 1.29 1.31 1.34

Delta H = K factor * Delta P 

# M0011

M0011-South-U2 Runs 1-3.xls K-Fs R1 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M0011

Common Stack

Normal

Run No: Run 2

Date: 4/28/2010

METER BOX ID: 90801 Orifice Delta H@: 1.730 Y FACTOR: 0.987

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.85 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.730 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 29.60 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 29.45 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 60 70 80 90

250 1.49 1.52 1.55 1.57

255 1.48 1.51 1.53 1.56

260 1.47 1.50 1.52 1.55

265 1.46 1.49 1.51 1.54

270 1.45 1.48 1.50 1.53

275 1.44 1.47 1.49 1.52

280 1.43 1.46 1.48 1.51

285 1.42 1.45 1.47 1.50

290 1.41 1.44 1.46 1.49

295 1.40 1.43 1.45 1.48

300 1.39 1.42 1.44 1.47

305 1.38 1.41 1.43 1.46

310 1.37 1.40 1.42 1.45

315 1.36 1.39 1.42 1.44

320 1.35 1.38 1.41 1.43

325 1.35 1.37 1.40 1.42

330 1.34 1.36 1.39 1.41

335 1.33 1.35 1.38 1.41

340 1.32 1.35 1.37 1.40

345 1.31 1.34 1.36 1.39

350 1.30 1.33 1.35 1.38

355 1.30 1.32 1.35 1.37

360 1.29 1.31 1.34 1.36

365 1.28 1.31 1.33 1.35

370 1.27 1.30 1.32 1.35

375 1.27 1.29 1.31 1.34

Delta H = K factor * Delta P 

# M0011

M0011-South-U2 Runs 1-3.xls K-Fs R2 

# TRC Environmental Corporation

# ORIFICE FLOW RATE CALCULATION-K Factors 

# M0011

Common Stack

Normal

Run No: Run 3

Date: 4/28/2010

METER BOX ID: 90801 Orifice Delta H@: 1.730 Y FACTOR: 0.987

DATA INPUTS:

O

2 

# Assumed Oxygen Concentration 7.0 % by volume

CO

2 

# Assumed Carbon Dioxide Concentration 12.0 % by volume

Pbaro Bar. Pressure at Base of Stack 29.85 in. Hg

% H 2 

# 0 Assumed Moisture Content 8.0 %

Tstd Temperature (standard) 68 o 

# F

Cp Type S Pitot No. and Coeff. 0.84

Dn Nozzle # and Diameter 0.218 inches

Delta H@ Orifice Calibration Factor 1.730 in. H 2 

# 0

Elevation Elevation of Sampling Location 250 feet above grade

CALCULATIONS:

Ps (gauge) Assumed Static Pressure -2.0 in. H 2 

# O

Pbaro (corrected) Bar. Pressure at Sampling Location 29.60 in. Hg

Ps (abs) Stack Pressure at Sampling Elevation 29.45 in. Hg

Md Dry Molecular Weight 30.20 lb/lb*mole

Ms Wet Molecular Weight 29.22 lb/lb*mole

K factor

Tstack ( o 

# F) Tm ( o 

# F)= 55 65 75 85

270 1.43 1.46 1.49 1.52

275 1.42 1.45 1.48 1.51

280 1.41 1.44 1.47 1.50

285 1.40 1.43 1.46 1.49

290 1.40 1.42 1.45 1.48

295 1.39 1.41 1.44 1.47

300 1.38 1.40 1.43 1.46

305 1.37 1.39 1.42 1.45

310 1.36 1.39 1.41 1.44

315 1.35 1.38 1.40 1.43

320 1.34 1.37 1.39 1.42

325 1.33 1.36 1.38 1.41

330 1.32 1.35 1.38 1.40

335 1.32 1.34 1.37 1.39

340 1.31 1.33 1.36 1.38

345 1.30 1.32 1.35 1.38

350 1.29 1.32 1.34 1.37

355 1.28 1.31 1.33 1.36

360 1.28 1.30 1.33 1.35

365 1.27 1.29 1.32 1.34

370 1.26 1.29 1.31 1.33

375 1.25 1.28 1.30 1.33

380 1.25 1.27 1.29 1.32

385 1.24 1.26 1.29 1.31

390 1.23 1.25 1.28 1.30

395 1.22 1.25 1.27 1.30

Delta H = K factor * Delta P 

# M0011

M0011-South-U2 Runs 1-3.xls K-Fs R3 

# TRC Environmental Corporation

# NOZZLE SELECTION CALCULATIONS 

# M0011

Common Stack

Normal

CHECK ALL INPUTS

Hand Input or Check Links

Input By:

Run 1 Run 2 Run 3

Date: 4/28/2010 4/28/2010 4/28/2010

Bar. Pressure, Pbar, in. Hg 29.85 29.85 29.85

Stack Temp.(F), ts (from prev. run) 125.0 192.0 191.8

Stack Temp. (R), Ts 585 652 652

Meter Temp. (F), tm 70.0 74.4 90.0

Meter Temp. (R), Tm 530 534 550

Pitot Number 0.0 0.0 0.0

Pitot Coefficient, cp 0.84 0.84 0.84

delta P avg. (from prev. run), dP, in. H2O 

# 0.94 2.00 1.95

O2 avg. (from prev. run), % 5.50 6.54 6.49

CO2 avg. (from prev. run), % 12.00 12.61 12.64

Static Pressure (from prev. run), in. H2O 

# -0.40 -0.92 -0.92

Ps, in. Hg 29.821 29.782 29.782

Mwd, lb/lb mole, dry 30.14 30.28 30.28

% Moisture (from prev. run) 13.0 12.5 12.3

MD 0.870 0.875 0.877

Mws, lb/lb mole, wet 28.562 28.739 28.772

delta H, (for sampling rate), in. H2O 1.730 1.730 1.730

delta H@, in. H2O 1.730 1.730 1.730

Qm, dscfm 0.750 0.750 0.750

Desired Nozzle , inches 0.224 0.190 0.188



# For Standard Test: dH = dH@, and therefore, Qm will be 0.75 dscfm.

For Different Sampling Rate: Input selected dH to yield desired sampling rate.

Desired Nozzle:

SQRT(SQRT((Ts*Mws)/(Ps*dP))*(0.0357*Qm*Pbar)/(Tm*cp*MD)) M0011

M0011-South-U2 Runs 1-3.xlsNozzles 

# TRC Environmental Corporation

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: 00-Jan-00

LOCATION: Southampton PROJECT NO.: 170096-0030

UNIT: Common Stack PERSONNEL: TRC

CONDITION: Normal



# Data Input Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.



# M0011

Parameter SYMBOL UNITS DATA Data

Test Number Prelim. Run 1 Run 2 Run 3

Test Date 1/0/1900 4/28/2010 4/28/2010 4/28/2010

Start Time 09:45 12:45 15:40

Stop Time 11:51 14:55 17:50 3-RUN AVG.

Stack Diameter ds inches 318.00 96.00 96.00 96.00

Nozzle Diameter dn inches 0.218 0.218 0.218

Barometric Pressure Pbar in. Hg 29.85 29.85 29.85 29.85

Stack Static Pressure Pg in. H2O -0.92 -0.92 -0.92 -0.92

Pitot Coefficient cp none 0.84 0.84 0.84 0.84

Meter Calibration Factor Y none 0.9873 0.9873 0.9873

DH@ none 1.7300 1.7300 1.7300

Stack Gas Oxygen Content O2 % 6.535 6.488 6.496 6.506

Stack Gas Carbon Dioxide Content CO2 % 12.605 12.643 12.635 12.628

Net Moisture Gain (Impingers w/SiGel) Ww grams 350.2 335.1 327.0 337.4

Average Stack Temperature ts deg F 192.0 191.8 189.8 191.2

Average Meter Temperature tm deg F 74.6 78.0 82.2 78.3

Avg Delta H dH in. H2O 3.10 3.02 3.11 3.08

Average Square Root Delta H ASR dH in. H2O 1.758 1.734 1.760 1.750

Avg Velocity Head dP in. H2O 2.00 1.95 2.00 1.98

Average Square Root Delta P ASR dP in H2O 1.412 1.392 1.412 1.405

Gas Sample Volume Vm cu. ft. 117.488 115.681 118.602 117.257

Total Sampling Time min minutes 120 120 120

M0011-South-U2 Runs 1-3.xls/Data 6/18/2010 8:53 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 28-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Common Stack

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 1 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

a1 0 260.735 1.5 1.225 2.3 1.517 190 64 63

2 5 1.7 1.304 2.6 1.612 190 66 63

3 10 1.9 1.378 2.9 1.703 193 72 65

4 15 2.0 1.414 3.1 1.761 193 74 64

5 20 2.1 1.449 3.3 1.817 193 75 65

6 25 2.2 1.483 3.4 1.844 193 78 66

7 30 2.1 1.449 3.3 1.817 193 80 66

8 35 2.2 1.483 3.4 1.844 192 82 68

9 40 2.2 1.483 3.4 1.844 192 83 68

10 45 2.1 1.449 3.3 1.817 192 84 69

11 50 2.1 1.449 3.3 1.817 192 82 69

12 55 1.9 1.378 2.9 1.703 192 85 69

60 319.422

b1 60 319.513 1.4 1.183 2.2 1.483 187 77 71

2 6 5 1.7 1.304 2.6 1.612 190 81 70

3 7 0 1.9 1.378 2.9 1.703 191 83 69

4 7 5 2.0 1.414 3.1 1.761 192 80 68

5 8 0 2.1 1.449 3.3 1.817 192 83 69

6 8 5 2.2 1.483 3.4 1.844 193 86 70

7 9 0 2.2 1.483 3.4 1.844 193 86 71

8 9 5 2.2 1.483 3.4 1.844 192 88 71

9 100 2.1 1.449 3.3 1.817 193 86 71

10 105 2.1 1.449 3.3 1.817 193 87 72

11 110 2.2 1.483 3.4 1.844 193 89 73

12 115 1.9 1.378 2.9 1.703 193 87 72

Stop 120 378.314

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

120.0 117.488 2.000 1.412 3.10 1.758 192.0 74.6

Impinger Gain

impinger 1: 922.5 829.9 92.6 O2: 6.535 Start Time: 09:45

impinger 2: 914.9 704.7 210.2 CO2: 12.605 Stop Time: 11:51

impinger 3: 742.0 726.0 16.0

impinger 4: 631.1 625.9 5.2 Static Pressure (Port A): -0.92

si gel 894.2 868.0 26.2 Static Pressure (Port B): -0.92

Static Pressure (Avg.): -0.92

350.2 DIFF

PRESS. 

# M0011 

# Field Data Run Sheets

M0011-South-U2 Runs 1-3.xls/Run 1 6/18/2010 8:53 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 28-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Common Stack

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 2 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

a1 0 378.507 2.0 1.414 3.1 1.761 191 67 66

2 5 2.1 1.449 3.3 1.817 191 73 67

3 10 2.1 1.449 3.3 1.817 191 77 67

4 15 2.2 1.483 3.4 1.844 191 81 69

5 20 2.2 1.483 3.4 1.844 191 82 69

6 25 2.2 1.483 3.4 1.844 191 83 69

7 30 2.2 1.483 3.4 1.844 191 84 70

8 35 2.2 1.483 3.4 1.844 191 87 71

9 40 2.1 1.449 3.3 1.817 192 87 72

10 45 2.2 1.483 3.4 1.844 192 89 74

11 50 2.0 1.414 3.1 1.761 192 87 73

12 55 2.0 1.414 3.1 1.761 193 87 74

60 439.210

b1 60 439.315 1.5 1.225 2.3 1.517 190 74 72

2 6 5 1.6 1.265 2.5 1.581 190 79 72

3 7 0 1.8 1.342 2.8 1.673 192 84 73

4 7 5 1.9 1.378 2.9 1.703 193 85 72

5 8 0 2.0 1.414 3.1 1.761 193 83 73

6 8 5 2.0 1.414 3.1 1.761 193 87 72

7 9 0 2.0 1.414 3.1 1.761 193 90 75

8 9 5 1.8 1.342 2.8 1.673 194 90 75

9 100 2.2 1.483 3.4 1.844 194 89 75

10 105 1.6 1.265 2.5 1.581 194 92 76

11 110 1.4 1.183 2.2 1.483 190 90 75

12 115 1.4 1.183 2.2 1.483 190 90 75

Stop 120 494.293

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

120.0 115.681 1.946 1.392 3.02 1.734 191.8 78.0

Impinger Gain

impinger 1: 965.7 830.3 135.4 O2: 6.488 Start Time: 12:45

impinger 2: 865.7 720.7 145.0 CO2: 12.643 Stop Time: 14:55

impinger 3: 721.9 700.0 21.9

impinger 4: 638.4 632.6 5.8 Static Pressure (Port A): -0.92

si gel 1016.8 989.8 27.0 Static Pressure (Port B): -0.92

Static Pressure (Avg.): -0.92

335.1 DIFF

PRESS. 

# M0011 

# Field Data Run Sheets

M0011-South-U2 Runs 1-3.xls/Run 2 6/18/2010 8:53 PM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion DATE: 28-Apr-10

LOCATION: Southampton PROJECT NO.: 170096-0030

LOAD: Normal PERSONNEL: TRC

UNIT: Common Stack

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

RUN NO: Run 3 PAGE ONE OF ONE

Minutes per reading: 5 OPERATOR:

number of readings: 24

DGM STACK DRY GAS METER

POINT TIME READING VEL. Sqrt TEMP. TEMP ( o 

# F)

NUMBER 

# INITIAL Dp (in. H 2 

# O) Dp DH Sqrt. ( o 

# F) INLET OUTLET

a1 0 494.446 1.5 1.225 2.3 1.517 187 77 71

2 5 1.6 1.265 2.5 1.581 187 81 71

3 10 1.8 1.342 2.8 1.673 188 86 72

4 15 1.9 1.378 2.9 1.703 189 87 72

5 20 2.0 1.414 3.1 1.761 189 90 74

6 25 2.0 1.414 3.1 1.761 190 90 75

7 30 2.2 1.483 3.4 1.844 190 90 76

8 35 2.3 1.517 3.6 1.897 190 92 76

9 40 2.0 1.414 3.1 1.761 190 93 77

10 45 2.0 1.414 3.1 1.761 191 92 78

11 50 1.8 1.342 2.8 1.673 191 92 78

12 55 1.8 1.342 2.8 1.673 191 91 77

60 552.453

b1 552.539 1.5 1.225 2.3 1.517 188 77 76

2 6 5 1.8 1.342 2.8 1.673 188 83 76

3 7 0 2.0 1.414 3.1 1.761 191 86 75

4 7 5 2.1 1.449 3.3 1.817 191 89 75

5 8 0 2.2 1.483 3.4 1.844 191 90 75

6 8 5 2.3 1.517 3.6 1.897 191 91 76

7 9 0 2.3 1.517 3.6 1.897 191 90 76

8 9 5 2.3 1.517 3.6 1.897 191 92 77

9 100 2.2 1.483 3.4 1.844 190 93 77

10 105 2.2 1.483 3.4 1.844 190 93 77

11 110 2.1 1.449 3.3 1.817 190 93 78

12 115 2.1 1.449 3.3 1.817 190 94 78

Stop 120 613.134

Total Total Avg. Avg. Avg. Avg. Avg. Avg.

120.0 118.602 2.000 1.412 3.11 1.760 189.8 82.2

Impinger Gain

impinger 1: 943.7 828.1 115.6 O2: 6.496 Start Time: 15:40

impinger 2: 877.5 706.5 171.0 CO2: 12.635 Stop Time: 17:50

impinger 3: 740.7 725.4 15.3

impinger 4: 629.7 626.2 3.5 Static Pressure (Port A): -0.92

si gel 915.8 894.2 21.6 Static Pressure (Port B): -0.92

Static Pressure (Avg.): -0.92

327.0 DIFF

PRESS. 

# M0011 

# Field Data Run Sheets

M0011-South-U2 Runs 1-3.xls/Run 3 6/18/2010 8:53 PM

# L2010-275 

# APPENDIX B

FIELD REDUCED DATA

# L2010-275 

# APPENDIX B.1

HCL, HF, AND HCN CALCULATION SHEETS

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: 29-Apr-10

LOCATION: Southhampton PROJECT NO.: 170096-0030

UNIT: Unit Common PERSONNEL: TRC

CONDITION: Normal

M26A/CTM033

Parameter SYMBOL UNITS

Test Number Run 1 Run 2 Run 3

Test Date 29-Apr-10 29-Apr-10 29-Apr-10

Start Time 750 1127 1459

Stop Time 1107 1432 1812

Calculated Data 3-RUN AVG.

Nozzle Area, An=3.14159*(dn/2)^2 An sq. in. 0.0373 0.0373 0.0373 0.0373

Stack Area,As As sq.ft. 50.27 50.27 50.27 50.27

Avg Stack Temperature, Ts=ts+460 Ts deg R 652.3 653.3 653.1 652.9

Meter Pressure, Pm=Pb+Dh/13.6 Pm in. Hg 30.48 30.48 30.48 30.48

Avg Meter Temperature, Tm=tm+460 Tm deg R 541.4 541.3 546.3 543.0

Gas Sample Volume at Standard Conditions, Vm(std) cu. ft. 174.593 176.261 170.685 173.846

Vm(std)= 528/29.92*Y*Vm*Pm/Tm cu. m. 4.943 4.990 4.832 4.922

Net Moisture Gain (Impingers w/SiGel) Ww grams 627.8 602.0 709.5 646.4

Volume of Water Vapor, Vw(std)= 0.04715*Wlc Vw(std) cu. ft. 29.601 28.384 33.453 30.479

Moisture Fraction, Bws = Vw(Std)/(Vm(Std)+Vw(Std))*100 Bws % 14.50% 13.87% 16.39% 14.92%

Dry Stack Gas Molecular Weight, Mwd g/g-mole 30.25 30.25 30.27 30.26

Md = (0.32*O2)+(0.44*CO2)+(0.28*(100-(O2+CO2)))

Wet Stack Gas Molecular Weight Mws g/g-mole 28.47 28.55 28.26 28.43

Mw = Md* (1-Bws)+(18*(Bws))

Absolute Stack Pressure, Ps = Pbar + Pg/13.6 Ps in. Hg. 30.18 30.18 30.18 30.18

Stack Gas Velocity

Vs= 85.49*Cp*ASRdP*((Ts)/((Ps)*(Mw)))^0.5 Vs ft/sec 88.89 88.84 88.32 88.68

Vsm = 0.3048* Vs Vsm m/sec 27.09 27.08 26.92 27.03

Actual Stack Gas Flow Rate, Qa = 60*Vs*As Qa acf/min 268,092 267,923 266,357 267,457

Stack Gas Flow Rate (STP), Qsw scf/min 218,893 218,420 217,185 218,166

Qsw = 528/29.92 * Qa * (Ps/Ts)

Dry Stack Gas Flow Rate (Dry, STP), Qsd dscf/min 187,161 188,125 181,594 185,627

Qsd = 528/29.92 * Qa * (1-Bws)* (Ps/Ts) dscm/min 5298.5 5325.8 5140.9 5255.1

Isokinetic Rate, I % 100.50 100.94 101.26 100.90

I =100*As*Vm(std)/min*(An/144)*Qsd

Meter Calibration (Alternate Method) Yqa none 1.0031 0.9943 1.0104 1.0026

Meter Quality Assurance/Quality Check % Diff -1.6% -0.7% -2.3% -1.6%

=100*(Y-Yqa)/Y PASS

Parameter SYMBOL UNITS Run 1 Run 2 Run 3 3-RUN AVG.

Total Sampling Time min minutes 180 180 180 180

Stack Gas Oxygen Content O2 % 6.72 6.67 6.49 6.63

Stack Gas Carbon Dioxide Content CO2 % 12.37 12.37 12.57 12.44

Gas Sample Volume at Standard Conditions, Vm(std) cu. ft. 174.593 176.261 170.685 173.846

cu. m. 4.943 4.990 4.832 4.922

Dry Stack Gas Flow Rate (Dry, STP), Qsd dscf/min 187,161.3 188,125.1 181,593.9 185,626.8

dscm/min 5,298.5 5,325.8 5,140.9 5,255.1



# Emissions Summary

Parameter UNITS Run 1 Run 2 Run 3 AVG

F-Factor 9780 9780 9780 9780

Emissions Summary - HCL

Total catch mg <0.401 <0.434 <0.450 <0.428

Concentration mg/dscf <0.002 <0.002 <0.003 <0.002

Concentration mg/dscm <0.081 <0.087 <0.093 <0.087

Emission Rate lb/hr <0.057 <0.061 <0.063 <0.060

Emission Rate lb/MMbtu <7.30E-05 <7.80E-05 <8.24E-05 <7.78E-05

Emissions Summary - HF

Total catch mg <0.387 <0.419 <0.435 <0.414

Concentration mg/dscf <0.002 <0.002 <0.003 <0.002

Concentration mg/dscm <0.078 <0.084 <0.090 <0.084

Emission Rate lb/hr <0.055 <0.059 <0.061 <0.058

Emission Rate lb/MMbtu <7.04E-05 <7.53E-05 <7.97E-05 <7.51E-05

Emissions Summary - HCN

Total catch ug 2199 1870 2457 2175.333

Concentration ug/dscf 12.595 10.609 14.395 12.533

Concentration ug/dscm 444.897 374.754 508.474 442.708

Emission Rate lb/hr 3.118 2.640 3.458 3.072

Emission Rate lb/MMbtu 4.00E-03 3.36E-03 4.50E-03 3.95E-03 

# Sampling Data Summary Yqa=Min/Vm*((0.0319*Tm*29)/(DH@*(Pbar+dH/13.6)*Md)) ^0.5 

# *ASRdH 

# Calculation Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

DATA

M26A-ctm033-South-U-common Runs 1-3.xls/Calculations 6/18/2010 8:27 PM

# L2010-275 

# APPENDIX B.2

PARTICULATE MATTER CALCULATION SHEETSSummary of Results - High LoadSouthamptonCommon StackFranklin,VARun 1Run 2Run 3Run IDPM2.5-10/OTM028-R1 PM2.5-10/OTM028-R2 PM2.5-10/OTM028-R3Test Date4/26/20104/27/20104/27/2010Run Start Time11:007:5014:11Run Finish Time17:2413:4719:49Net Traverse Points121212ThetaNet Run Time, Minutes369.50320.50332.5DiaNozzle Diameter, Inches0.1380.1260.126CpPitot tube Coeffecient0.840.840.84YDry Gas Meter Calibration Factor0.99650.99650.9965PbarBarometric Pressure, "Hg30.053029.25Delta HAverage Differential Pressure of Orifice, ft30.440.430.440.44VmVolume of Metered Gas Sample, ft3141.857118.9122.339127.699tmAverage Temp. of Dry Gas Meter,oF78.3 64.3 65.9 69.5VmstdVolume of Stack Gas Metered At Standard Conditions, ft3139.343119.710119.737126.263vlVolume of Liquid Collected in Impingers, g432.5365392396.5VwstdVolume of Water Standard20.3617.1818.4518.66% H20Percent Moisture by Volume12.7512.5513.3512.88MfdDry Mole Fraction0.8730.8740.8660.871%CO2Percent Carbon Dioxide12.683 13.101 13.17813.0%O2Percent Oxygen6.5456.0675.9956.20%CO-N2Percent Carbon Monoxide and Nitrogen80.880.880.82780.8FoFuel Factor1.131.131.131.13MdGas Molecular Weight, Dry30.2930.3430.3530.33MwGas Molecular Weight, Wet28.7228.7928.7028.74PgStatic Pressure, "H2O-0.85-0.85-0.85-0.85PsAbsolute Flue Gas Pressure, "Hg29.9929.9429.1929.70tsAverage Flue Gas Temp.,oF188.8187.8185.1187.2Delta-pAverage Velocity Head, "H2O2.1101.9812.0192.037vsFlue Gas Velocity, ft/sec90.5287.6289.5589.23AStack/Duct Area, in27,238.27,238.27,238.27,238.2QsdVolumetric Flow, DSCFM194,220188,374186,786189,793QmsdVolumetric Flow, DSCMM5,500.35,334.85,289.85,374.9QawVolumetric Flow, ACFM272,995264,249270,089269,111%IPercent IsoKinetics93.9115.1111.9107.0FdFuel Factor9780978097809780MMBtu/hrAproximate Heat input818.39820.19817.22818.60VsStack Gas Viscosity194.21193.92192.52193.55QsPM10 Flow, @ Cyclone Conditions, ACFM0.5300.5240.5210.525D50Dia of Particles in Cyclone I, Microns9.699.759.809.75NreReynolds Number Actual3129.7 3104.5 3033.4 3089.2CactCunningham Correction Factor @ Stack Conditions1.071.071.071.07D50(Nre<3162)Particulate Cut Diameter for Nre<3162 for Cyclone IV2.042.072.102.07D50(Nre≥3162)Particulate Cut Diameter for Nre≥3162 for Cyclone IV2.042.052.062.05CrRe-estimated Cunningham Correction Factor1.091.091.091.09D50-1Re-calculate Particle Cut Diameter for Nre<31622.032.052.082.05D50-1Re-calculate Particle Cut Diameter for Nre≥31622.022.042.052.04Z (Nre≥3162)Ratio (Z) Between D50and D50-1Values0.9930.9930.9930.993Z (Nre<3162)Ratio (Z) Between D50and D50-1Values0.9930.9930.9930.993Acceptance Criteria for Z Values (Nre≥3162)PASSPASSPASSAcceptance Criteria for Z Values (Nre<3163)PASSPASSPASSAverageSummary of Results - High LoadSouthamptonCommon StackFranklin,VARun 1Run 2Run 3Run IDPM2.5-10/OTM028-R1 PM2.5-10/OTM028-R2 PM2.5-10/OTM028-R3Test Date4/26/20104/27/20104/27/2010Run Start Time11:007:5014:11Run Finish Time17:2413:4719:49Averagemg<D50Less than 2.5 Microns, mg4.45.34.94.87mg<D50greater than 2.5 Microns, mg36.135.129.333.50%<D50Percent less than 2.5 Microns11131413%<D50Percent greater than 2.5 Microns89878687mg Organic CPMOrganic Condensible PM, mg9.32.81.54.53mg Inorganic CPM Inorganic Condensible PM, mg16.67.27.610.47mg CPMTotal CPM*23.98.07.113.00lb/MMBtuEmission Rate, lb/MMBtu0.00540.00200.00183.07E-03PM2.5 including CPM Total Milligrams Collected After Cyclone Separator ("IDEM PM2.5")28.313.312.017.9gr/DSCFConcentration, grains/DSCF0.003130.001710.001550.00213mg/DSCMConcentration, mg/DSCM7.173.923.544.88lb/hrPM2.5 Emission Rate, lb/hr5.2182.7682.4763.487lb/MMBtuEmission Rate, lb/MMBtu0.00640.00340.00300.0043PM2.5 excluding CPM Total Milligrams Collected After Cyclone Separator w/o CPM4.45.34.94.9gr/DSCFConcentration, grains/DSCF0.000490.000680.000630.00060mg/DSCMConcentration, mg/DSCM1.121.561.451.37lb/hrPM2.5 Emission Rate, lb/hr0.8111.1031.0110.975lb/MMBtuEmission Rate, lb/MMBtu0.00100.00130.00121.19E-03* Total CPM reported is adjusted for maximum allowable field blank correction of 2.0 mg.

# TEST DATA:

Run number PM2.5-10/OTM028-R1 PM2.5-10/OTM028-R2 PM2.5-10/OTM028-R3

Date 4/26/2010 4/27/2010 4/27/2010

Start Time 11:00 7:50 14:11

Finish Time 17:24 13:47 19:49

Laboratory Resolution Resolution Resolution

GRAVIMETRIC RESULTS (grams)

Filterable Particulate Matter < PM 2.5 (OTM 027)

Filter weight gain, milligrams 3.5000 80% 4.4000 83% 3.3000 67%

Acetone rinse weight gain, milligrams 0.9000 20% 0.9000 17% 1.6000 33%

Total filterable PM < 2.5 Microns 4.4000 5.3000 4.9000

Filterable Particulate Matter > PM 2.5(OTM 027)

Filter weight gain, milligrams N/A 0% 0% 0%

Acetone rinse weight gain, milligrams 36.1000 100% 35.1000 100% 29.3000 100%

Total filterable PM < 10 & > 2.5 Microns 36.1000 35.1000 29.3000

Condensible Particulate Matter (OTM 028)

Organic condensible PM weight gain, milligrams 9.3000 36% 2.8000 28% 1.5000 16%

Inorganic condensible PM weight gain, milligra m 16.6000 64% 7.2000 72% 7.6000 84%

Total condensible PM 25.9000 10.0000 9.1000

Total PM 10/PM2.5 (C\OTM 027 and 028)

Total filterable PM, milligrams 40.5000 61% 40.4000 80% 34.2000 79%

Total condensible PM, milligrams 25.9000 39% 10.0000 20% 9.1000 21%

Total filterable and condensible PM, mg 66.4000 50.4000 43.3000

ND - Compound was not detected 

# Southampton

Franklin,VA

Common Stack

OTM027/OTM028

# L2010-275 

# APPENDIX B.3

METALS CALCULATION SHEETS

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: 00-Jan-00

LOCATION: Southampton PROJECT NO.: 170096-0030

UNIT: Unit 1 and 2 PERSONNEL: TRC

CONDITION: Normal

M29

Parameter SYMBOL UNITS

Test Number Run 1 Run 2 Run 3

Test Date 26-Apr-10 27-Apr-10 27-Apr-10

Start Time 12:00 09:00 14:45

Stop Time 16:07 13:05 19:05

Calculated Data 3-RUN AVG.

Nozzle Area, An=3.14159*(dn/2)^2 An sq. in. 0.0373 0.0373 0.0373 0.0373

Stack Area,As As sq.ft. 50.27 50.27 50.27 50.27

Avg Stack Temperature, Ts=ts+460 Ts deg R 649.5 647.3 646.2 647.7

Meter Pressure, Pm=Pb+Dh/13.6 Pm in. Hg 29.32 29.35 29.36 29.34

Avg Meter Temperature, Tm=tm+460 Tm deg R 553.1 544.5 541.3 546.3

Gas Sample Volume at Standard Conditions, Vm(std) cu. ft. 232.253 220.990 224.365 225.869

Vm(std)= 528/29.92*Y*Vm*Pm/Tm cu. m. 6.575 6.256 6.352 6.394

Net Moisture Gain (Impingers w/SiGel) Ww grams 781.3 726.3 755.0 754.2

Volume of Water Vapor, Vw(std)= 0.04715*Wlc Vw(std) cu. ft. 36.838 34.245 35.598 35.561

Moisture Fraction, Bws = Vw(Std)/(Vm(Std)+Vw(Std))*100 Bws % 13.69% 13.42% 13.69% 13.60%

Dry Stack Gas Molecular Weight, Mwd g/g-mole 30.29 30.34 30.35 30.33

Md = (0.32*O2)+(0.44*CO2)+(0.28*(100-(O2+CO2)))

Wet Stack Gas Molecular Weight Mws g/g-mole 28.61 28.68 28.66 28.65

Mw = Md* (1-Bws)+(18*(Bws))

Absolute Stack Pressure, Ps = Pbar + Pg/13.6 Ps in. Hg. 29.01 29.06 29.06 29.04

Stack Gas Velocity

Vs= 85.49*Cp*ASRdP*((Ts)/((Ps)*(Mw)))^0.5 Vs ft/sec 93.88 88.26 89.29 90.48

Vsm = 0.3048* Vs Vsm m/sec 28.61 26.90 27.22 27.58

Actual Stack Gas Flow Rate, Qa = 60*Vs*As Qa acf/min 283,130 266,178 269,296 272,868

Stack Gas Flow Rate (STP), Qsw scf/min 223,139 210,918 213,733 215,930

Qsw = 528/29.92 * Qa * (Ps/Ts)

Dry Stack Gas Flow Rate (Dry, STP), Qsd dscf/min 192,592 182,619 184,465 186,559

Qsd = 528/29.92 * Qa * (1-Bws)* (Ps/Ts) dscm/min 5452.3 5170.0 5222.2 5281.5

Isokinetic Rate, I % 97.44 97.78 98.28 97.83

I =100*As*Vm(std)/min*(An/144)*Qsd

Meter Calibration (Alternate Method) Yqa none 1.0131 1.0138 1.0141 1.0136

Meter Quality Assurance/Quality Check % Diff -2.6% -2.7% -2.7% -2.7%

=100*(Y-Yqa)/Y PASS

Parameter SYMBOL UNITS Run 1 Run 2 Run 3 3-RUN AVG.

Total Sampling Time min minutes 240 240 240 240

Stack Gas Oxygen Content O2 % 6.545 6.067 5.995 6.202

Stack Gas Carbon Dioxide Content CO2 % 12.683 13.101 13.178 12.987

Gas Sample Volume at Standard Conditions, Vm(std) cu. ft. 232.253 220.990 224.365 225.869

cu. m. 6.575 6.256 6.352 6.394

Dry Stack Gas Flow Rate (Dry, STP), Qsd dscf/min 192,591.7 182,619.3 184,465.2 186,558.7

dscm/min 5,452.3 5,170.0 5,222.2 5,281.5 

# Sampling Data Summary Yqa=Min/Vm*((0.0319*Tm*29)/(DH@*(Pbar+dH/13.6)*Md)) ^0.5 

# *ASRdH 

# Calculation Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

DATA

M29-South - U Common Runs 1-3.xls/Calculations 6/22/2010 11:39 AM

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: 00-Jan-00

LOCATION: Southampton PROJECT NO.: 170096-0030

UNIT: Unit 1 and 2 PERSONNEL: TRC

CONDITION: Normal

M29

Parameter SYMBOL UNITS

Test Number Run 1 Run 2 Run 3

Test Date 26-Apr-10 27-Apr-10 27-Apr-10

Start Time 12:00 09:00 14:45

Stop Time 16:07 13:05 19:05

Calculated Data 3-RUN AVG. 

# Calculation Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

DATA



# Metal Emissions Summary

Parameter UNITS Run 1 Run 2 Run 3 AVG

F-Factor mg 9780 9780 9780 9780

Emissions Summary - Antimony

Total catch ug <0.808 <0.621 <0.530 <0.530

Concentration ug/dscf <0.0035 <0.0028 <0.0024 <0.0029

Concentration ug/dscm <0.123 <0.099 <0.083 <0.102

Emission Rate lb/hr <0.0001 <0.0001 <0.0001 <0.0001

Emission Rate lb/MMbtu <1.09E-07 <8.54E-08 <7.14E-08 <8.87E-08

Emissions Summary - Arsenic

Total catch ug <0.248 <0.202 <0.171 <0.207

Concentration ug/dscf <0.0011 <0.0009 <0.0008 <0.0009

Concentration ug/dscm <0.038 <0.032 <0.027 <0.032

Emission Rate lb/hr <0.0000 <0.0000 <0.0000 <0.0000

Emission Rate lb/MMbtu <3.35E-08 <2.78E-08 <2.30E-08 <2.81E-08

Emissions Summary - Beryllium

Total catch ug <0.476 <0.366 <0.344 <0.395

Concentration ug/dscf <0.0020 <0.0017 <0.0015 <0.0017

Concentration ug/dscm <0.072 <0.059 <0.054 <0.062

Emission Rate lb/hr <0.0001 <0.0000 <0.0000 <0.0000

Emission Rate lb/MMbtu <6.43E-08 <5.03E-08 <4.64E-08 <5.37E-08

Emissions Summary - Cadmium

Total catch ug <0.327 <0.152 <0.150 <0.210

Concentration ug/dscf <0.0014 <0.0007 <0.0007 <0.0009

Concentration ug/dscm <0.050 <0.024 <0.024 <0.033

Emission Rate lb/hr <0.0000 <0.0000 <0.0000 <0.0000

Emission Rate lb/MMbtu <4.42E-08 <2.09E-08 <2.02E-08 <2.84E-08

Emissions Summary - Chromium

Total catch ug 12.870 5.870 6.550 8.430

Concentration ug/dscf 0.0554 0.0266 0.0292 0.04

Concentration ug/dscm 1.96 0.94 1.03 1.31

Emission Rate lb/hr 0.0014 0.0006 0.0007 0.0009

Emission Rate lb/MMbtu 1.74E-06 8.07E-07 8.83E-07 1.14E-06

Emissions Summary - Cobalt

Total catch ug <2.410 <1.780 <1.780 <1.990

Concentration ug/dscf <0.0104 <0.0081 <0.0079 <0.0088

Concentration ug/dscm <0.367 <0.285 <0.280 <0.310

Emission Rate lb/hr <0.0003 <0.0002 <0.0002 <0.0002

Emission Rate lb/MMbtu <3.26E-07 <2.45E-07 <2.40E-07 <2.70E-07

Emissions Summary - Lead

Total catch ug 6.150 4.810 4.294 5.085

Concentration ug/dscf 0.03 0.02 0.02 0.02

Concentration ug/dscm 0.94 0.77 0.68 0.79

Emission Rate lb/hr 0.0007 0.0005 0.0005 0.0006

Emission Rate lb/MMbtu 8.31E-07 6.61E-07 5.79E-07 6.90E-07

Emissions Summary - Manganese

Total catch ug 13.920 5.440 5.000 8.120

Concentration ug/dscf 0.06 0.02 0.02 0.04

Concentration ug/dscm 2.12 0.87 0.79 1.26

Emission Rate lb/hr 0.0015 0.0006 0.0005 0.0009

Emission Rate lb/MMbtu 1.88E-06 7.48E-07 6.74E-07 1.10E-06

Emissions Summary - Nickel

Total catch ug 15.530 11.780 12.390 13.233

Concentration ug/dscf 0.07 0.05 0.06 0.06

Concentration ug/dscm 2.36 1.88 1.95 2.07

Emission Rate lb/hr 0.0017 0.0013 0.0013 0.0014

Emission Rate lb/MMbtu 2.10E-06 1.62E-06 1.67E-06 1.80E-06

Emissions Summary - Selenium

Total catch ug <3.590 <3.470 <3.030 <3.363

Concentration ug/dscf <0.0155 <0.0157 <0.0135 <0.0149

Concentration ug/dscm <0.546 <0.555 <0.477 <0.526

Emission Rate lb/hr <0.0004 <0.0004 <0.0003 <0.0004

Emission Rate lb/MMbtu <4.85E-07 <4.77E-07 <4.08E-07 <4.57E-07

M29-South - U Common Runs 1-3.xls/Calculations 6/22/2010 11:39 AM

# L2010-275 

# APPENDIX B.4

MERCURY CALCULATION SHEETS

# Method 30-B Sample Data

Source Southampton Date:

Instrument #REF!



# Calibration Data Estimated Hg Stack Concentration (for Recovery Study)

1/Mean RF #REF! 0.07



# Low Standard Response Factor

#REF! ng/area count



# Pair # 1

Trap Sample Volume Spike 50%-150% Section-1 Section-2 % C

rec 

# Spike % Spike

ID (dsL) Level (ng) of Sample? ng ng Breakthrough Conc, ug/m3 Recovery



# 57290 738.286 50 OK 417 0.4 0.1 0.079 117.3%

57291 702.545 341 0.3 0.1

Pair # 2

Trap Sample Volume Spike 50%-150% Section-1 Section-2 % C

rec 

# Spike % Spike

ID (dsL) Level (ng) of Sample? ng ng Breakthrough Conc, ug/m3 Recovery



# 57342 760.339 30 OK 269 0.3 0.1 0.060 151.9%

57343 704.442 207 0.1 0.0

Pair # 3

Trap Sample Volume Spike 50%-150% Section-1 Section-2 % C

rec 

# Spike % Spike

ID (dsL) Level (ng) of Sample? ng ng Breakthrough Conc, ug/m3 Recovery



# 57340 750.878 30 OK 153 0.7 0.5 0.036 90.0%

57306 703.280 118 0.5 0.4

Average Field Recovery Volume, dsL 726.63

Average Percent Recovery for Runs 1,2,3 119.8%

Average Percent Recovery for Runs 1 and 2 103.7%

Prepared By: ____________________________ (sign) ______________________________ (sign)

( Analyst) 

# #REF!

# Method 30-B Sample Data

Source Southampton Date:

Instrumen t #REF!



# Calibration Data

1/Mean RF #REF!



# Low Standard Response Factor

#REF! ng/area count



# Instrument Analytical Range Low (ng) High (ng) Is Source < 1.0 ug/dscm ? x

Initial Calbration #REF! #REF! Is Source > 1.0 ug/dscm ?

Bias Test 20 2000 If so, place an "X" in the box

Maximum % Breakthrough 

# 20

Maximum % Relative Deviation 

# 20

Pair # 1

Trap Volume Sam- Section-1 Section-1 Section-2 Section-2 % Hg Conc. % % of Recovery Average CO2

ID pled (dsL) A rea ng A rea ng Breakthrough ug/dscm Relative Deviation Study Volume ug/dscm % Lb/MMBtu



# 57290 738.286 367.0 0.4 0.1 0.498 1.2 102% 0.492 12.683 4.357E-07



# 57291 702.545 341.0 0.3 0.1 0.486 97%

Pair # 2

Trap Volume Sam- Section-1 Section-1 Section-2 Section-2 % Hg Conc. % % of Recovery Average

ID pled (dsL) A rea ng A rea ng Breakthrough ug/dscm Relative Deviation Study Volume ug/dscm



# 57342 760.339 239.0 0.3 0.1 0.315 3.4 105% 0.304 13.101 2.611E-07



# 57343 704.442 207.0 0.1 0.0 0.294 97%

Pair # 3

Trap Volume Sam- Section-1 Section-1 Section-2 Section-2 % Hg Conc. % % of Recovery Average

ID pled (dsL) A rea ng A rea ng Breakthrough ug/dscm Relative Deviation Study Volume ug/dscm



# 57340 750.878 123.0 0.7 0.6 0.165 1.1 103% 0.167 13.178 1.421E-07



# 57306 703.28 118.0 0.5 0.4 0.168 97%

2.796E-07

Prepared By: ____________________________ (sign) ______________________________ (sign)

( Analyst) (Project Manager or QA Manager ) 

# #REF!

# L2010-275 

# APPENDIX B.5

SO2, NOX AND CO CALCULATIONSRun averages corrected for biasOperator: M. MartinPlant NameDominion Southampton1.661E-07 1.194E-07Location: Common StackCEM StartEndSample Duration O2 CO2 SO2 NOxSO2 NOx F-Factor SO2 NOxRun file # Date Time Date Time Minutes % % ppm ppmppm @ 7% ppm @ 7%Lb/MMBtu Lb/MMBtu1 4/29/2010 7:50 4/29/2010 12:131806.72113.232 F11.43 228.14411.205 223.655 9780 0.027 0.3932 4/29/2010 12:50 4/29/2010 15:50180 6.673 12.371 10.871 228.9810.621 223.717 9780 0.026 0.3933 4/29/2010 16:06 4/29/2010 19:06180 6.489 12.57 13.876 230.5413.384 222.365 9780 0.033 0.390Avg11.737 223.2460.029 0.392Run averages corrected for biasOperator: M. MartinPlant NameDominion SouthamptonLocation: Common StackCEM StartEndSample Durat O2 CO2SO2 CO CH4 NMHCRun file # Date Time Date Time Minutes % %ppm ppm ppm ppm1 4/28/2010 9:48 4/28/2010 11:48 120 6.535 12.605 12.83 35.47 0.234 02 4/28/2010 12:52 4/28/2010 14:52 120 6.488 12.643 21.222 31.21 0.202 0.0013 4/28/2010 15:50 4/28/2010 17:50 120 6.496 12.635 6.587 36.19 0.238 0Run averages corrected for biasOperator: M. MartinPlant NameDominion SouthamptonLocation: Common StackCEM StartEndSaRun file # Date Time Date Time1 4/28/2010 9:48 4/28/2010 11:482 4/28/2010 12:52 4/28/2010 14:523 4/28/2010 15:50 4/28/2010 17:501.661E-07 7.267E-08 4.153E-08 1.142E-07SO2 CO CH4 NMHC F-Factor SO2 CO CH4 NMHCppm @ 7% ppm @ 7%ppm @ 7%ppm @ 7%Lb/MMBtu Lb/MMBtu Lb/MMBtu Lb/MMBtu12.415 34.322 0.226 0.000 9780 0.030 0.037 1.38E-04 0.0020.468 30.101 0.195 0.001 9780 0.050 0.032 1.19E-04 0.006.357 34.924 0.230 0.000 9780 0.016 0.037 1.40E-04 0.0013.080 33.1160.032 0.035

# L2010-275 

# APPENDIX B.6

THC AND METHANE CALCULATIONS

# Firm: Dominio n Anal y zer : 55C-73015-372

Location: Southham p to n S p an Value ( S ) :

O p erato r MPM Anal y zer Ran g e : 30

Sam p le Location: Common Stac k

Date: 28-A p r-1 0

TOTAL HYDROCARBONS

PRE-TEST Calibration Error Check:

C y linde r C y linde r Anal y ze r Predicte d Calibratio n

ID Gas Conc. Res p ons e Slo p e Res p ons e Error ( <5% )

-- ( Ca ) ( C ) ( m ) ( pr ) ( ce )

Zero, CO

-- 0.000 0.003

C3H8 low 

# (25-35% span) CC245111 7.001 6.836 0.9995 7.000 -2.35%

C3H8 mid 

# (45-55% span) CC155902 12.030 11.901 0.9995 12.027 -1.04%

C3H8 hi g h 

# (80-90% span) CC178755 24.860 24.850 0.9995

Calibration Dri f t Check:

Run No: 1 2 3

Time Av g

Non-Methane

Initial Zero C OI 

# 0.004 0.003 0.003

Initial Span C M I 

# 6.837 6.626 6.446

Final Zero C OF 

# 0.003 0.003 0.003

Final Span C M F 

# 6.626 6.446 6.716

Calibration Drift (< 3%) CD O 

# 0.0% 0.0% 0.0%

Calibration Drift (< 3%) CD M 

# 0.8% 0.7% -1.1%

C3H8 Conc. (ppm, wet) C

av g 

# 0.003 0.004 0.003 0.003

C3H8 Conc. (ppm, wet, corrected) C

av g 

# 0.003 0.004 0.003 0.003

Moisture content (% ) 10.72% 12.38% 12.14% 11.75%

C3H8 Conc. ( pp m, Dr y , corrected) 0.003 0.005 0.003 0.004

Ox yg en Concentration (% ) 6.535 6.488 6.496 6.506

C3H8 Conc. ( pp m, Dr y , @ 7%O2) 0.003 0.004 0.003 0.004

C3H8 (lb/MMBtu) 5.46E-06 7.42E-06 5.55E-06 6.14E-06

Nomenclature

C hi g h 

# Span gas analyzer response

C O 

# Zero gas analyzer response

C

a 

# Cylinder gas value

C OI 

# Initial calibration zero response

C OF 

# Final calibration zero response

C M I 

# Initial calibration upscale response

C M F 

# Final calibration upscale response

CDo Zero calibration drif t

CDm U p scale calibration drif t

m Slo p e

pr Predicted res p onse

ce Calibration erro r

C Anal y zer res p ons e

S S p an

C TH C 

# Total hydrocarbon concentration CEM CALIBRATION DATA

EPA Method 25A

24.860

# Firm: Dominio n Anal y zer : 55C-73015-372

Location: Southham p to n S p an Value ( S ) :

O p erato r MPM Anal y zer Ran g e : 30

Sam p le Location: Common Stac k

Date: 28-A p r-1 0

TOTAL HYDROCARBONS

PRE-TEST Calibration Error Check:

C y linde r C y linde r Anal y ze r Predicte d Calibratio n

ID Gas Conc. Res p ons e Slo p e Res p ons e Error ( <5% )

-- ( Ca ) ( C ) ( m ) ( pr ) ( ce )

Zero, CO

-- 0.000 0.36

CH4 low 

# (25-35% span) CC245111 7.049 7.093 0.9708 7.207 -1.6%

CH4 mid 

# (45-55% span) CC155902 12.050 12.108 0.9708 12.062 0.4%

CH4 hi g h 

# (80-90% span) CC178755 25.370 24.992 0.9708

Calibration Dri f t Check:

Run No: 1 2 3 4 5

Time Av g

Non-Methane

Initial Zero C OI 

# 0.336 0.395 0.245

Initial Span C M I 

# 7.094 6.973 6.804

Final Zero C OF 

# 0.395 0.245 0.304

Final Span C M F 

# 6.973 6.804 7.063

Calibration Drift (< 3%) CD O 

# -0.2% 0.6% -0.2%

Calibration Drift (< 3%) CD M 

# 0.5% 0.7% -1.0%

CH4 Conc. (ppm, wet) C

av g 

# 0.586 0.507 0.520 0.538

CH4 Conc. (ppm, wet, corrected) C

av g 

# 0.569 0.505 0.518 0.530

Moisture content (% ) 12.54% 12.38% 12.14% 12.35%

CH4 Conc. ( pp m, Dr y , corrected) 0.650 0.576 0.589 0.605

Ox yg en Concentration (% ) 6.535 6.488 6.496 6.506

CH4 Conc. ( pp m, Dr y , @ 7%O2) 0.63 0.56 0.57 0.585

CH4 (lb/MMBtu) 3.84E-04 3.39E-04 3.47E-04 3.57E-04

Nomenclature

C hi g h 

# Span gas analyzer response

C O 

# Zero gas analyzer response

C

a 

# Cylinder gas value

C OI 

# Initial calibration zero response

C OF 

# Final calibration zero response

C M I 

# Initial calibration upscale response

C M F 

# Final calibration upscale response

CDo Zero calibration drif t

CDm U p scale calibration drif t

m Slo p e

pr Predicted res p onse

ce Calibration erro r

C Anal y zer res p ons e

S S p an

C TH C 

# Total hydrocarbon concentration CEM CALIBRATION DATA

EPA Method 25A

25.370

# L2010-275 

# APPENDIX B.7

FORMALDEHYDE CALCULATION SHEET

# TRC Environmental Corp.

EMISSION MEASUREMENTS DEPARTMENT

Wannalancit Mills, 650 Suffolk Street

Lowell, MA 01854

Phone: (978) 970-5600

Fax: (978) 453-4215

CLIENT: Dominion Dates: 00-Jan-00

LOCATION: Southampton PROJECT NO.: 170096-0030

UNIT: Common Stack PERSONNEL: TRC

CONDITION : Normal

M0011

Parameter SYMBOL UNITS

Test Number Run 1 Run 2 Run 3

Test Date 28-Apr-10 28-Apr-10 28-Apr-10

Start Time 09:45 12:45 15:40

Stop Time 11:51 14:55 17:50

Calculated Data 3-RUN AVG.

Nozzle Area, An=3.14159*(dn/2)^2 An sq. in. 0.0373 0.0373 0.0373 0.0373

Stack Area,As As sq.ft. 50.27 50.27 50.27 50.27

Avg Stack Temperature, Ts=ts+460 Ts deg R 652.0 651.8 649.8 651.2

Meter Pressure, Pm=Pb+Dh/13.6 Pm in. Hg 30.08 30.07 30.08 30.08

Avg Meter Temperature, Tm=tm+460 Tm deg R 534.6 538.0 542.2 538.3

Gas Sample Volume at Standard Conditions, Vm(std) cu. ft. 115.172 112.663 114.636 114.157

Vm(std)= 528/29.92*Y*Vm*Pm/Tm cu. m. 3.261 3.189 3.245 3.232

Net Moisture Gain (Impingers w/SiGel) Ww grams 350.2 335.1 327.0 337.4

Volume of Water Vapor, Vw(std)= 0.04715*Wlc Vw(std) cu. ft. 16.512 15.800 15.418 15.910

Moisture Fraction, Bws = Vw(Std)/(Vm(Std)+Vw(Std))*100 Bws % 12.54% 12.30% 11.86% 12.23%

Dry Stack Gas Molecular Weight, Mwd g/g-mole 30.28 30.28 30.28 30.28

Md = (0.32*O2)+(0.44*CO2)+(0.28*(100-(O2+CO2)))

Wet Stack Gas Molecular Weight Mws g/g-mole 28.74 28.77 28.83 28.78

Mw = Md* (1-Bws)+(18*(Bws))

Absolute Stack Pressure, Ps = Pbar + Pg/13.6 Ps in. Hg. 29.78 29.78 29.78 29.78

Stack Gas Velocity

Vs= 85.49*Cp*ASRdP*((Ts)/((Ps)*(Mw)))^0.5 Vs ft/sec 88.49 87.16 88.19 87.94

Vsm = 0.3048* Vs Vsm m/sec 26.97 26.57 26.88 26.81

Actual Stack Gas Flow Rate, Qa = 60*Vs*As Qa acf/min 266,871 262,856 265,969 265,232

Stack Gas Flow Rate (STP), Qsw scf/min 215,136 211,954 215,124 214,071

Qsw = 528/29.92 * Qa * (Ps/Ts)

Dry Stack Gas Flow Rate (Dry, STP), Qsd dscf/min 188,160 185,885 189,621 187,889

Qsd = 528/29.92 * Qa * (1-Bws)* (Ps/Ts) dscm/min 5326.8 5262.4 5368.2 5319.1

Isokinetic Rate, I % 98.92 97.95 97.70 98.19

I =100*As*Vm(std)/min*(An/144)*Qsd

Meter Calibration (Alternate Method) Yqa none 1.0057 1.0110 1.0044 1.0071

Meter Quality Assurance/Quality Check % Diff -1.9% -2.4% -1.7% -2.0%

=100*(Y-Yqa)/Y PASS

Parameter SYMBOL UNITS Run 1 Run 2 Run 3 3-RUN AVG.

Total Sampling Time min minutes 120 120 120 120

Stack Gas Oxygen Content O2 % 6.535 6.488 6.496 6.506

Stack Gas Carbon Dioxide Content CO2 % 12.605 12.643 12.635 12.628

Gas Sample Volume at Standard Conditions, Vm(std) cu. ft. 115.172 112.663 114.636 114.157

cu. m. 3.261 3.189 3.245 3.232

Dry Stack Gas Flow Rate (Dry, STP), Qsd dscf/min 188,160.1 185,885.0 189,620.6 187,888.6

dscm/min 5,326.8 5,262.4 5,368.2 5,319.1



# Emissions Summary

Parameter UNITS Run 1 Run 2 Run 3 AVG

F-Factor 9780 9780 9780 9780

Emissions Summary - HCOH

Total catch ug 68.2 51.8 93.0 71.0

Concentration ug/dscf 0.592 0.460 0.811 0.621

Concentration ug/dscm 20.917 16.241 28.656 21.938

Concentration ppm 1.70E-02 1.32E-02 2.33E-02 1.79E-02

Concentration ppm @ 7%O2 1.65E-02 1.28E-02 2.25E-02 1.72E-02

Emission Rate lb/hr 0.147 0.113 0.203 0.155

Emission Rate lb/MMbtu 1.86E-05 1.44E-05 2.54E-05 1.94E-05 

# Sampling Data Summary Yqa=Min/Vm*((0.0319*Tm*29)/(DH@*(Pbar+dH/13.6)*Md)) ^0.5



# *ASRdH 

# Calculation Sheet

The table below contains the results of testing and calculations performed by TRC on the date(s) listed.

DATA

M0011-South-U2 Runs 1-3.xls/Calculations 6/18/2010 8:53 PM

# L2010-275 

# APPENDIX B.8

VOLATILE ORGANIC HAPS

CALCULATION SHEETEIA Facility CodeFacility Name Boiler IDs:10774 Southampton Pow1_2* Front half fraction contains first Tenax tube results** Back half fraction contains second Tenax and Anasorb tube resultsSpeciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the total for each pollutant.FractionMeasuredValue(μg/m3)BasisTest Method UsedData Flag (ADL,BDL, DDL)Test MethodCommentslb/mmBtu μg/dscm @ 7% O2Methyl chloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<1.43] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.27E-06][<1.38]545.5Methyl chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<1.63] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<1.44E-06][<1.57]545.5Methyl chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<3.05] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.71E-06][<2.95]545.5Methyl chloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.98] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<8.71E-07][<0.95]545.5Methyl chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<1.72] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.53E-06][<1.66]545.5Methyl chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<2.70] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.40E-06][<2.61]545.5Methyl chloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<8.77E-07][<0.96]546Methyl chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<1.48] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.32E-06][<1.43]546Methyl chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<2.47] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<2.19E-06][<2.39]546Vinyl chloride (chloroethene)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<8.73E-07][<0.95]545.5Vinyl chloride (chloroethene)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<6.55E-07][<0.71]545.5Vinyl chloride (chloroethene)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<1.72] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.53E-06][<1.66]545.5Vinyl chloride (chloroethene)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.98] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<8.71E-07][<0.95]545.5Vinyl chloride (chloroethene)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Vinyl chloride (chloroethene)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<2.21] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.96E-06][<2.14]545.5Vinyl chloride (chloroethene)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<8.77E-07][<0.96]546Vinyl chloride (chloroethene)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Vinyl chloride (chloroethene)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<2.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.97E-06][<2.15]546Methyl bromide14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<2.04] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.81E-06][<1.97]545.5Methyl bromide1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.83] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<7.31E-07][<0.80]545.5Methyl bromide1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<2.87] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.54E-06][<2.77]545.5Methyl bromide24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.98] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<8.71E-07][<0.95]545.5Methyl bromide2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<4.79] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.25E-06][<4.63]545.5Methyl bromide2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<5.78] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<5.12E-06][<5.58]545.5Methyl bromide34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<8.77E-07][<0.96]546Methyl bromide3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Methyl bromide3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<2.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.97E-06][<2.15]546Ethyl chloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.10E-06][<1.20]545.5Ethyl chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<1.47] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<1.30E-06][<1.41]545.5Ethyl chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<2.71] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.40E-06][<2.62]545.5Ethyl chloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<1.41] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.25E-06][<1.36]545.5Ethyl chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<1.54] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.36E-06][<1.48]545.5Ethyl chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<2.95] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.61E-06][<2.85]545.5Ethyl chloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<1.46] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.29E-06][<1.41]546Ethyl chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<1.48] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.32E-06][<1.43]546Ethyl chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<2.94] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.61E-06][<2.84]546Carbon disulfide14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* 2.88 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report2.55E-062.78545.5Carbon disulfide1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.96] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<8.51E-07][<0.93]545.5Carbon disulfide1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<3.84] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<3.40E-06][<3.71]545.5Carbon disulfide24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* 2.79 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report2.47E-062.69545.5Carbon disulfide2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<1.44] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.27E-06][<1.39]545.5Carbon disulfide2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<4.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<3.75E-06][<4.08]545.5Carbon disulfide34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* 1.60 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report1.41E-061.54546Carbon disulfide3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.93] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.22E-07][<0.90]546Carbon disulfide3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<2.52] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.24E-06][<2.44]546Vinylidene chloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Vinylidene chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.42] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.71E-07][<0.40]545.5Vinylidene chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.91] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.08E-07][<0.88]545.5Vinylidene chloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Vinylidene chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Vinylidene chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Vinylidene chloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Vinylidene chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Vinylidene chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Methylene chloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* 19.89 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report1.76E-0519.20545.5Methylene chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** 39.42 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLincomplete tube analyses -F3.49E-0538.05545.5Methylene chloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total59.31 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report5.26E-0557.25545.5Methylene chloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* 11.08 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report9.81E-0610.69545.5Methylene chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<26.60] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.36E-05][<25.68]545.5Methylene chloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<37.68] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<3.34E-05][<36.37]545.5Methylene chloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<6.59] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<5.84E-06][<6.36]546Methylene chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<3.80] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<3.37E-06][<3.67]546Methylene chloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<10.39] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<9.21E-06][<10.03]546Ethylidene dichloride (1,1-dichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Ethylidene dichloride (1,1-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.42] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.71E-07][<0.40]545.5Ethylidene dichloride (1,1-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.91] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.08E-07][<0.88]545.5Ethylidene dichloride (1,1-dichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Ethylidene dichloride (1,1-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Ethylidene dichloride (1,1-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Ethylidene dichloride (1,1-dichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Ethylidene dichloride (1,1-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Ethylidene dichloride (1,1-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Methyl ethyl ketone (2-butanone)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Methyl ethyl ketone (2-butanone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<1.50] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<1.33E-06][<1.45]545.5Methyl ethyl ketone (2-butanone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<2.00] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.77E-06][<1.93]545.5Methyl ethyl ketone (2-butanone)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Methyl ethyl ketone (2-butanone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<10.33] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.15E-06][<9.97]545.5Methyl ethyl ketone (2-butanone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<10.82] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.59E-06][<10.44]545.5Methyl ethyl ketone (2-butanone)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End DateVolatile Organic HAP Emission Test ResultsTest End TimeCalculated Emission RateSteam Output(1000 lb/hr)EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionMethyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinyl chloride (chloroethene) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinyl chloride (chloroethene) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinyl chloride (chloroethene) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl bromide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl bromide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl bromide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon disulfide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon disulfide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon disulfide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinylidene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinylidene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinylidene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethylene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethylene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethylene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylidene dichloride (1,1-dichloroethane) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylidene dichloride (1,1-dichloroethane) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylidene dichloride (1,1-dichloroethane) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl ethyl ketone (2-butanone) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl ethyl ketone (2-butanone) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl ethyl ketone (2-butanone) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeFuel InputRateFuel TypeUnits ofMeasureMeasurementMethodFuel InputRateFuel Type802.58.9 12.6 6.5 194,970191.927.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.0512.5 12.6 6.5 192,598191.927.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.612.4 12.6 6.5 190,870190.327.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminousTotal HeatInput(mmBtu/hr)Flue GasCO2(%)Flue GasMoisture (%)Flue GasTemperature (F)Flue GasO2(%)Flue Gas FlowRate (dscfm)Fuel #1FueEIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionMethyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinyl chloride (chloroethene) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinyl chloride (chloroethene) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinyl chloride (chloroethene) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl bromide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl bromide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl bromide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon disulfide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon disulfide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon disulfide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinylidene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinylidene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinylidene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethylene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethylene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethylene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylidene dichloride (1,1-dichloroethane) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylidene dichloride (1,1-dichloroethane) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylidene dichloride (1,1-dichloroethane) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl ethyl ketone (2-butanone) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl ethyl ketone (2-butanone) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl ethyl ketone (2-butanone) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeUnits ofMeasureMeasurementMethodFuel InputRateFuel TypeUnits ofMeasureMeasurementMethodFuel Input Rate Fuel TypeUnits ofMeasureMeasurementMethodFuel #4el #2Fuel #3EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionMethyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinyl chloride (chloroethene) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinyl chloride (chloroethene) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinyl chloride (chloroethene) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl bromide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl bromide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl bromide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon disulfide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon disulfide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon disulfide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinylidene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinylidene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinylidene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethylene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethylene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethylene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylidene dichloride (1,1-dichloroethane) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylidene dichloride (1,1-dichloroethane) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylidene dichloride (1,1-dichloroethane) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl ethyl ketone (2-butanone) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl ethyl ketone (2-butanone) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl ethyl ketone (2-butanone) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeSet a Set b Set c Set dRun No.μgμgμgμgMethyl chloride1T1 0.035 0.041 < 0.020 < 0.020Methyl chloride1T2/ANA < 0.020< 0.020 0.092Methyl chloride1TOTAL < 0.055 0.041 < 0.040 < 0.112Methyl chloride2T1 < 0.020 < 0.020 < 0.020 < 0.020Methyl chloride2T2/ANA 0.040 < 0.020 < 0.020 < 0.020 <Methyl chloride2TOTAL < 0.060 < 0.040 < 0.040 < 0.040 <Methyl chloride3T1 < 0.020 < 0.020 < 0.020 < 0.020Methyl chloride3T2/ANA < 0.020 < 0.020 < 0.020 < 0.020 <Methyl chloride3TOTAL < 0.040 < 0.040 < 0.040 < 0.040 <Vinyl chloride (chloroethene)1T1 < 0.020 < 0.020 < 0.020 < 0.020Vinyl chloride (chloroethene)1T2/ANA < 0.020< 0.020 < 0.020Vinyl chloride (chloroethene)1TOTAL < 0.040 < 0.020 < 0.040 < 0.040Vinyl chloride (chloroethene)2T1 < 0.020 < 0.020 < 0.020 < 0.020Vinyl chloride (chloroethene)2T2/ANA < 0.020 < 0.020 < 0.020 < 0.020 <Vinyl chloride (chloroethene)2TOTAL < 0.040 < 0.040 < 0.040 < 0.040 <Vinyl chloride (chloroethene)3T1 < 0.020 < 0.020 < 0.020 < 0.020Vinyl chloride (chloroethene)3T2/ANA < 0.020 < 0.020 < 0.020 < 0.020 <Vinyl chloride (chloroethene)3TOTAL < 0.040 < 0.040 < 0.040 < 0.040 <Methyl bromide1T1 0.069 0.057 < 0.020 < 0.020Methyl bromide1T2/ANA < 0.020< 0.020 0.027Methyl bromide1TOTAL < 0.089 0.057 < 0.040 < 0.047Methyl bromide2T1 < 0.020 < 0.020 < 0.020 < 0.020Methyl bromide2T2/ANA 0.037 0.216 0.097 < 0.020 <Methyl bromide2TOTAL < 0.057 < 0.236 < 0.117 < 0.040 <Methyl bromide3T1 < 0.020 < 0.020 < 0.020 < 0.020Methyl bromide3T2/ANA < 0.020 < 0.020 < 0.020 < 0.020 <Methyl bromide3TOTAL < 0.040 < 0.040 < 0.040 < 0.040 <Ethyl chloride1T1 < 0.020 < 0.020 < 0.020 0.041Ethyl chloride1T2/ANA < 0.020< 0.020 0.079Ethyl chloride1TOTAL < 0.040 < 0.020 < 0.040 0.120Ethyl chloride2T1 0.035 0.027 < 0.020 0.033Ethyl chloride2T2/ANA < 0.020 < 0.020 < 0.020 0.025 <Ethyl chloride2TOTAL < 0.055 < 0.047 < 0.040 0.058 <Ethyl chloride3T1 0.058 < 0.020 < 0.020 < 0.020Ethyl chloride3T2/ANA < 0.020 < 0.020 < 0.020 < 0.020 <Ethyl chloride3TOTAL < 0.078 < 0.040 < 0.040 < 0.040 <Carbon disulfide1T1 0.043 0.051 0.054 0.086Carbon disulfide1T2/ANA 0.023< 0.010 0.045Carbon disulfide1TOTAL 0.066 0.051 < 0.064 0.131Carbon disulfide2T1 0.052 0.048 0.063 0.064Carbon disulfide2T2/ANA 0.025 < 0.010 0.026 0.036 <Carbon disulfide2TOTAL 0.077 < 0.058 0.089 0.100 <Carbon disulfide3T1 0.044 0.030 0.024 0.031Carbon disulfide3T2/ANA 0.018 < 0.010 < 0.010 0.017 <Carbon disulfide3TOTAL 0.062 < 0.040 < 0.034 0.048 <Vinylidene chloride1T1 < 0.010 < 0.010 < 0.010 < 0.010Vinylidene chloride1T2/ANA 0.014< 0.010 < 0.010Vinylidene chloride1TOTAL < 0.024 < 0.010 < 0.020 < 0.020Vinylidene chloride2T1 < 0.010 < 0.010 < 0.010 < 0.010Vinylidene chloride2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Vinylidene chloride2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Vinylidene chloride3T1 < 0.010 < 0.010 < 0.010 < 0.010Vinylidene chloride3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Vinylidene chloride3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Methylene chloride1T1 0.144 0.480 0.385 0.606Methylene chloride1T2/ANA 0.1020.142 2.957Methylene chloride1TOTAL 0.246 0.480 0.527 3.563Methylene chloride2T1 0.218 0.203 0.233 0.247Methylene chloride2T2/ANA 0.090 1.295 0.448 0.311 <Methylene chloride2TOTAL 0.308 1.498 0.681 0.558 <Methylene chloride3T1 0.317 0.121 < 0.070 0.025Methylene chloride3T2/ANA 0.209 0.051 0.013 0.014 <Methylene chloride3TOTAL 0.526 0.172 < 0.083 0.039 <Ethylidene dichloride (1,1-dichloroetha1T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylidene dichloride (1,1-dichloroetha1T2/ANA 0.014< 0.010 < 0.010Ethylidene dichloride (1,1-dichloroetha1TOTAL < 0.024 < 0.010 < 0.020 < 0.020Ethylidene dichloride (1,1-dichloroetha2T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylidene dichloride (1,1-dichloroetha2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Ethylidene dichloride (1,1-dichloroetha2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Ethylidene dichloride (1,1-dichloroetha3T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylidene dichloride (1,1-dichloroetha3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Ethylidene dichloride (1,1-dichloroetha3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Methyl ethyl ketone (2-butanone)1T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl ethyl ketone (2-butanone)1T2/ANA 0.102< 0.010 < 0.010Methyl ethyl ketone (2-butanone)1TOTAL < 0.112 < 0.010 < 0.020 < 0.020Methyl ethyl ketone (2-butanone)2T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl ethyl ketone (2-butanone)2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Methyl ethyl ketone (2-butanone)2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Methyl ethyl ketone (2-butanone)3T1 < 0.010 < 0.010 < 0.010 < 0.010Other Supporting InformationEIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionMethyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinyl chloride (chloroethene) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinyl chloride (chloroethene) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinyl chloride (chloroethene) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinyl chloride (chloroethene) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinyl chloride (chloroethene) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinyl chloride (chloroethene) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl bromide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl bromide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl bromide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl bromide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl bromide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl bromide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthyl chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethyl chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthyl chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethyl chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthyl chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethyl chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon disulfide 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon disulfide 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon disulfide 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon disulfide 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon disulfide 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon disulfide 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalVinylidene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Vinylidene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalVinylidene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Vinylidene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalVinylidene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Vinylidene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethylene chloride 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methylene chloride 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethylene chloride 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methylene chloride 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethylene chloride 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methylene chloride 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylidene dichloride (1,1-dichloroethane) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylidene dichloride (1,1-dichloroethane) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylidene dichloride (1,1-dichloroethane) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylidene dichloride (1,1-dichloroethane) 3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl ethyl ketone (2-butanone) 14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl ethyl ketone (2-butanone) 1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl ethyl ketone (2-butanone) 24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl ethyl ketone (2-butanone) 2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl ethyl ketone (2-butanone) 34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeCondTotalTotalμgμgRun No.Set aSet b Set c Set d dsL------ < 0.116119.5420.57 20.56 20.54 81.20------< 0.132119.5420.57 20.56 20.54 81.20< 0.0440.000 < 0.248119.5420.57 20.56 20.5481.20< 0.044------ < 0.080 ND220.4720.32 20.34 20.22 81.35------0.040 < 0.140220.4720.32 20.34 20.22 81.35< 0.040.040 < 0.220220.4720.32 20.34 20.2281.35< 0.04------ < 0.080 ND320.3420.23 20.16 20.11 80.83------0.040 < 0.120 ND320.3420.23 20.16 20.11 80.83< 0.040.040 < 0.200 ND320.3420.23 20.16 20.1180.83< 0.04------ < 0.080 ND119.5420.57 20.56 20.54 81.20------< 0.060119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.140119.5420.57 20.56 20.5481.20< 0.02------ < 0.080 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.100 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.180 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.080 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.100 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.180 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.166119.5420.57 20.56 20.54 81.20------< 0.067119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.233119.5420.57 20.56 20.5481.20< 0.02------ < 0.080 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.390220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.470220.4720.32 20.34 20.2281.35< 0.02------ < 0.080 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.100 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.180 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.101119.5420.57 20.56 20.54 81.20------< 0.119119.5420.57 20.56 20.54 81.20< 0.040.000 < 0.220119.5420.57 20.56 20.5481.20< 0.04------ < 0.115220.4720.32 20.34 20.22 81.35------0.040 < 0.125220.4720.32 20.34 20.22 81.35< 0.040.040 < 0.240220.4720.32 20.34 20.2281.35< 0.04------ < 0.118320.3420.23 20.16 20.11 80.83------0.040 < 0.120 ND320.3420.23 20.16 20.11 80.83< 0.040.040 < 0.238320.3420.23 20.16 20.1180.83< 0.04------0.234119.5420.57 20.56 20.54 81.20------< 0.078119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.312119.5420.57 20.56 20.5481.20< 0.02------0.227220.4720.32 20.34 20.22 81.35------0.020 < 0.117220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.344220.4720.32 20.34 20.2281.35< 0.02------0.129320.3420.23 20.16 20.11 80.83------0.020 < 0.075320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.204320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.034119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.074119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------1.615119.5420.57 20.56 20.54 81.20------3.201119.5420.57 20.56 20.54 81.20< 0.020.000 4.816119.5420.57 20.56 20.5481.20< 0.02------0.901220.4720.32 20.34 20.22 81.35------0.020 < 2.164220.4720.32 20.34 20.22 81.35< 0.020.020 < 3.065220.4720.32 20.34 20.2281.35< 0.02------ < 0.533320.3420.23 20.16 20.11 80.83------0.020 < 0.307320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.840320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.034119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.074119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.122119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.162119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.800 < 0.840 ND220.4720.32 20.34 20.22 81.35< 0.020.800 < 0.880 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------Sample Volume (dsL)EIA Facility CodeFacility Name Boiler IDs:10774 Southampton Pow1_2* Front half fraction contains first Tenax tube results** Back half fraction contains second Tenax and Anasorb tube resultsSpeciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the total for each pollutant.FractionMeasuredValue(μg/m3)BasisTest Method UsedData Flag (ADL,BDL, DDL)Test MethodCommentslb/mmBtu μg/dscm @ 7% O2Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End DateVolatile Organic HAP Emission Test ResultsTest End TimeCalculated Emission RateSteam Output(1000 lb/hr)Methyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<10.39] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.21E-06][<10.03]546Methyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<10.89] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.65E-06][<10.51]546Chloroform14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.37] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.27E-07][<0.36]545.5Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.86] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.64E-07][<0.83]545.5Chloroform24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Chloroform34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Methyl chloroform (1,1,1-trichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.37] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.27E-07][<0.36]545.5Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.86] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.64E-07][<0.83]545.5Methyl chloroform (1,1,1-trichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Methyl chloroform (1,1,1-trichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Carbon tetrachloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<6.28] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<5.57E-06][<6.06]545.5Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<6.77] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<6.00E-06][<6.54]545.5Carbon tetrachloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Carbon tetrachloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Ethylene dichloride (1,2-dichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.96] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.51E-07][<0.93]545.5Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<3.92] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.47E-06][<3.78]545.5Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<4.88] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.32E-06][<4.71]545.5Ethylene dichloride (1,2-dichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.95] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.39E-07][<0.91]545.5Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.90] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.95E-07][<0.87]545.5Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.84] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.63E-06][<1.78]545.5Ethylene dichloride (1,2-dichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.66] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<5.81E-07][<0.63]546Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.40] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.24E-06][<1.35]546Benzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* 0.94 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report8.29E-070.90545.5Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<3.65] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.23E-06][<3.52]545.5Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<4.58] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.06E-06][<4.42]545.5Benzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* 0.68 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report5.99E-070.65545.5Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.93] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.28E-07][<0.90]545.5Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.61] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.43E-06][<1.55]545.5Benzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* 0.74 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report6.58E-070.72546Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<1.15] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.02E-06][<1.11]546Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.89] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.68E-06][<1.83]546Trichloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.37] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.27E-07][<0.36]545.5Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.86] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.64E-07][<0.83]545.5Trichloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Trichloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Propylene dichloride (1,2-dichloropropane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.60] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<5.35E-07][<0.58]545.5Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<1.10] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<9.71E-07][<1.06]545.5Propylene dichloride (1,2-dichloropropane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Propylene dichloride (1,2-dichloropropane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]5461,3-Dichloropropene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.51,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.39] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.49E-07][<0.38]545.51,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.89] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.86E-07][<0.86]545.51,3-Dichloropropene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.51,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.51,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.51,3-Dichloropropene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]5461,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]5461,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Methyl isobutyl ketone (hexone)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.37] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLincomplete tube analyses -F[<3.27E-07][<0.36]545.5Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.86] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.64E-07][<0.83]545.5Methyl isobutyl ketone (hexone)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Methyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<10.33] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.15E-06][<9.97]545.5EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChloroform14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChloroform24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChloroform34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl chloroform (1,1,1-trichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloroform (1,1,1-trichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloroform (1,1,1-trichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon tetrachloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon tetrachloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon tetrachloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dichloride (1,2-dichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dichloride (1,2-dichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dichloride (1,2-dichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalBenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalBenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalBenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTrichloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTrichloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTrichloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalPropylene dichloride (1,2-dichloropropane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalPropylene dichloride (1,2-dichloropropane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalPropylene dichloride (1,2-dichloropropane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,3-Dichloropropene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,3-Dichloropropene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,3-Dichloropropene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl isobutyl ketone (hexone)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl isobutyl ketone (hexone)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Fuel InputRateFuel TypeUnits ofMeasureMeasurementMethodFuel InputRateFuel TypeTotal HeatInput(mmBtu/hr)Flue GasCO2(%)Flue GasMoisture (%)Flue GasTemperature (F)Flue GasO2(%)Flue Gas FlowRate (dscfm)Fuel #1Fue796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminousEIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChloroform14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChloroform24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChloroform34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl chloroform (1,1,1-trichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloroform (1,1,1-trichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloroform (1,1,1-trichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon tetrachloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon tetrachloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon tetrachloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dichloride (1,2-dichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dichloride (1,2-dichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dichloride (1,2-dichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalBenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalBenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalBenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTrichloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTrichloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTrichloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalPropylene dichloride (1,2-dichloropropane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalPropylene dichloride (1,2-dichloropropane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalPropylene dichloride (1,2-dichloropropane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,3-Dichloropropene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,3-Dichloropropene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,3-Dichloropropene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl isobutyl ketone (hexone)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl isobutyl ketone (hexone)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Units ofMeasureMeasurementMethodFuel InputRateFuel TypeUnits ofMeasureMeasurementMethodFuel Input Rate Fuel TypeUnits ofMeasureMeasurementMethodFuel #4el #2Fuel #3EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChloroform14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChloroform24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChloroform34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl chloroform (1,1,1-trichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloroform (1,1,1-trichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloroform (1,1,1-trichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon tetrachloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon tetrachloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon tetrachloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dichloride (1,2-dichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dichloride (1,2-dichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dichloride (1,2-dichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalBenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalBenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalBenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTrichloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTrichloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTrichloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalPropylene dichloride (1,2-dichloropropane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalPropylene dichloride (1,2-dichloropropane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalPropylene dichloride (1,2-dichloropropane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,3-Dichloropropene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,3-Dichloropropene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,3-Dichloropropene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl isobutyl ketone (hexone)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl isobutyl ketone (hexone)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Set a Set b Set c Set dRun No.μgμgμgμgOther Supporting InformationMethyl ethyl ketone (2-butanone)3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Methyl ethyl ketone (2-butanone)3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Chloroform1T1 < 0.010 < 0.010 < 0.010 < 0.010Chloroform1T2/ANA < 0.010< 0.010 < 0.010Chloroform1TOTAL < 0.020 < 0.010 < 0.020 < 0.020Chloroform2T1 < 0.010 < 0.010 < 0.010 < 0.010Chloroform2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Chloroform2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Chloroform3T1 < 0.010 < 0.010 < 0.010 < 0.010Chloroform3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Chloroform3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Methyl chloroform (1,1,1-trichloroetha 1T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl chloroform (1,1,1-trichloroetha 1T2/ANA < 0.010< 0.010 < 0.010Methyl chloroform (1,1,1-trichloroetha 1TOTAL < 0.020 < 0.010 < 0.020 < 0.020Methyl chloroform (1,1,1-trichloroetha 2T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl chloroform (1,1,1-trichloroetha 2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Methyl chloroform (1,1,1-trichloroetha 2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Methyl chloroform (1,1,1-trichloroetha 3T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl chloroform (1,1,1-trichloroetha 3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Methyl chloroform (1,1,1-trichloroetha 3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Carbon tetrachloride1T1 < 0.010 < 0.010 < 0.010 < 0.010Carbon tetrachloride1T2/ANA 0.2500.250 < 0.010Carbon tetrachloride1TOTAL < 0.260 < 0.010 < 0.260 < 0.020Carbon tetrachloride2T1 < 0.010 < 0.010 < 0.010 < 0.010Carbon tetrachloride2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Carbon tetrachloride2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Carbon tetrachloride3T1 < 0.010 < 0.010 < 0.010 < 0.010Carbon tetrachloride3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Carbon tetrachloride3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Ethylene dichloride (1,2-dichloroethan1T1 < 0.010 0.022 0.023 0.023Ethylene dichloride (1,2-dichloroethan1T2/ANA 0.287< 0.010 0.021Ethylene dichloride (1,2-dichloroethan1TOTAL < 0.297 0.022 < 0.033 0.044Ethylene dichloride (1,2-dichloroethan2T1 0.022 < 0.010 0.023 0.022Ethylene dichloride (1,2-dichloroethan2T2/ANA < 0.010 < 0.010 < 0.010 0.023 <Ethylene dichloride (1,2-dichloroethan2TOTAL < 0.032 < 0.020 < 0.033 0.045 <Ethylene dichloride (1,2-dichloroethan3T1 0.023 < 0.010 < 0.010 < 0.010Ethylene dichloride (1,2-dichloroethan3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Ethylene dichloride (1,2-dichloroethan3TOTAL < 0.033 < 0.020 < 0.020 < 0.020 <Benzene1T1 0.021 0.016 0.013 0.026Benzene1T2/ANA < 0.010< 0.266 0.020Benzene1TOTAL < 0.031 0.016 < 0.279 0.046Benzene2T1 0.012 0.014 0.014 0.015Benzene2T2/ANA < 0.010 0.024 0.012 < 0.010 <Benzene2TOTAL < 0.022 0.038 0.026 < 0.025 <Benzene3T1 0.015 0.014 0.014 0.017Benzene3T2/ANA 0.011 0.014 0.034 0.014 <Benzene3TOTAL 0.026 0.028 0.048 0.031 <Trichloroethylene1T1 < 0.010 < 0.010 < 0.010 < 0.010Trichloroethylene1T2/ANA < 0.010< 0.010 < 0.010Trichloroethylene1TOTAL < 0.020 < 0.010 < 0.020 < 0.020Trichloroethylene2T1 < 0.010 < 0.010 < 0.010 < 0.010Trichloroethylene2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Trichloroethylene2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Trichloroethylene3T1 < 0.010 < 0.010 < 0.010 < 0.010Trichloroethylene3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Trichloroethylene3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Propylene dichloride (1,2-dichloroprop1T1 < 0.010 < 0.010 < 0.010 < 0.010Propylene dichloride (1,2-dichloroprop1T2/ANA 0.0290.010 < 0.010Propylene dichloride (1,2-dichloroprop1TOTAL < 0.039 < 0.010 < 0.020 < 0.020Propylene dichloride (1,2-dichloroprop2T1 < 0.010 < 0.010 < 0.010 < 0.010Propylene dichloride (1,2-dichloroprop2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Propylene dichloride (1,2-dichloroprop2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Propylene dichloride (1,2-dichloroprop3T1 < 0.010 < 0.010 < 0.010 < 0.010Propylene dichloride (1,2-dichloroprop3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Propylene dichloride (1,2-dichloroprop3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <1,3-Dichloropropene1T1 < 0.010 < 0.010 < 0.010 < 0.0101,3-Dichloropropene1T2/ANA < 0.010< 0.010 0.0121,3-Dichloropropene1TOTAL < 0.020 < 0.010 < 0.020 < 0.0221,3-Dichloropropene2T1 < 0.010 < 0.010 < 0.010 < 0.0101,3-Dichloropropene2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <1,3-Dichloropropene2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <1,3-Dichloropropene3T1 < 0.010 < 0.010 < 0.010 < 0.0101,3-Dichloropropene3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <1,3-Dichloropropene3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Methyl isobutyl ketone (hexone)1T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl isobutyl ketone (hexone)1T2/ANA < 0.010< 0.010 < 0.010Methyl isobutyl ketone (hexone)1TOTAL < 0.020 < 0.010 < 0.020 < 0.020Methyl isobutyl ketone (hexone)2T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl isobutyl ketone (hexone)2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl ethyl ketone (2-butanone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChloroform14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chloroform1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChloroform24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chloroform2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChloroform34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chloroform3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl chloroform (1,1,1-trichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl chloroform (1,1,1-trichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl chloroform (1,1,1-trichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl chloroform (1,1,1-trichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalCarbon tetrachloride14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Carbon tetrachloride1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCarbon tetrachloride24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Carbon tetrachloride2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalCarbon tetrachloride34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Carbon tetrachloride3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dichloride (1,2-dichloroethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dichloride (1,2-dichloroethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dichloride (1,2-dichloroethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dichloride (1,2-dichloroethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dichloride (1,2-dichloroethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dichloride (1,2-dichloroethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalBenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Benzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalBenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Benzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalBenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Benzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTrichloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Trichloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTrichloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Trichloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTrichloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Trichloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalPropylene dichloride (1,2-dichloropropane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Propylene dichloride (1,2-dichloropropane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalPropylene dichloride (1,2-dichloropropane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Propylene dichloride (1,2-dichloropropane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalPropylene dichloride (1,2-dichloropropane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Propylene dichloride (1,2-dichloropropane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,3-Dichloropropene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,3-Dichloropropene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,3-Dichloropropene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,3-Dichloropropene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,3-Dichloropropene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,3-Dichloropropene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalMethyl isobutyl ketone (hexone)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Methyl isobutyl ketone (hexone)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalMethyl isobutyl ketone (hexone)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Methyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**CondTotalTotalμgμgRun No.Set aSet b Set c Set d dsLSample Volume (dsL)0.800 < 0.840 ND320.3420.23 20.16 20.11 80.83< 0.020.800 < 0.880 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.030119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.070119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.030119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.070119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.510119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.550119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.078119.5420.57 20.56 20.54 81.20------< 0.318119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.396119.5420.57 20.56 20.5481.20< 0.02------ < 0.077220.4720.32 20.34 20.22 81.35------0.020 < 0.073220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.150220.4720.32 20.34 20.2281.35< 0.02------ < 0.053320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.113320.3420.23 20.16 20.1180.83< 0.02------0.076119.5420.57 20.56 20.54 81.20------< 0.296119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.372119.5420.57 20.56 20.5481.20< 0.02------0.055220.4720.32 20.34 20.22 81.35------0.020 < 0.076220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.131220.4720.32 20.34 20.2281.35< 0.02------0.060320.3420.23 20.16 20.11 80.83------0.020 < 0.093320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.153320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.030119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.070119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.049119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.089119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.032119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.072119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.030119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.070119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.800 < 0.840 ND220.4720.32 20.34 20.22 81.35< 0.02EIA Facility CodeFacility Name Boiler IDs:10774 Southampton Pow1_2* Front half fraction contains first Tenax tube results** Back half fraction contains second Tenax and Anasorb tube resultsSpeciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the total for each pollutant.FractionMeasuredValue(μg/m3)BasisTest Method UsedData Flag (ADL,BDL, DDL)Test MethodCommentslb/mmBtu μg/dscm @ 7% O2Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End DateVolatile Organic HAP Emission Test ResultsTest End TimeCalculated Emission RateSteam Output(1000 lb/hr)Methyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<10.82] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.59E-06][<10.44]545.5Methyl isobutyl ketone (hexone)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<10.39] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.21E-06][<10.03]546Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<10.89] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<9.65E-06][<10.51]5461,1,2-Trichloroethane14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.51,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.37E-07][<0.48]545.51,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.73E-07][<0.95]545.51,1,2-Trichloroethane24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.51,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.51,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.51,1,2-Trichloroethane34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]5461,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]5461,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Toluene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* 2.19 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report1.94E-062.12545.5Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.87] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.75E-07][<0.84]545.5Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<3.07] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.72E-06][<2.96]545.5Toluene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* 1.84 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report1.63E-061.78545.5Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<2.64] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.34E-06][<2.55]545.5Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<4.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<3.98E-06][<4.33]545.5Toluene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.95] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.44E-07][<0.92]546Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.82] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.24E-07][<0.79]546Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.77] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.57E-06][<1.71]546Tetrachloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.81] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<7.20E-07][<0.78]545.5Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<14.41] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.28E-05][<13.91]545.5Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<15.22] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.35E-05][<14.69]545.5Tetrachloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* 1.06 Dry U.S. EPA Method 0031 with SW-846 Method 8260BADLFor M0031 we are report9.37E-071.02545.5Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.79] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.59E-06][<1.73]545.5Tetrachloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.56] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.93E-07][<0.54]546Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.30] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.15E-06][<1.25]546Ethylene dibromide (1,2-dibromoethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.37E-07][<0.48]545.5Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.73E-07][<0.95]545.5Ethylene dibromide (1,2-dibromoethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Ethylene dibromide (1,2-dibromoethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Chlorobenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.37E-07][<0.48]545.5Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.73E-07][<0.95]545.5Chlorobenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Chlorobenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Ethylbenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.37E-07][<0.48]545.5Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.73E-07][<0.95]545.5Ethylbenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Ethylbenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Xylenes (isomer & mixtures)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<1.48] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.31E-06][<1.43]545.5Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<1.48] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<1.31E-06][<1.43]545.5Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<2.96] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<2.62E-06][<2.85]545.5Xylenes (isomer & mixtures)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<1.48] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.31E-06][<1.42]545.5Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<1.97] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.74E-06][<1.90]545.5Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<3.44] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<3.05E-06][<3.32]545.5Xylenes (isomer & mixtures)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<1.48] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.32E-06][<1.43]546Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<1.98] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.75E-06][<1.91]546Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<3.46] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<3.07E-06][<3.34]546o-Xylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.37E-07][<0.48]545.5o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.73E-07][<0.95]545.5o-Xylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5o-Xylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Styrene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.57] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<5.02E-07][<0.55]545.5Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<1.06] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<9.38E-07][<1.02]545.5EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl isobutyl ketone (hexone)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,1,2-Trichloroethane14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,1,2-Trichloroethane24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,1,2-Trichloroethane34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalToluene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalToluene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalToluene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTetrachloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTetrachloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTetrachloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dibromide (1,2-dibromoethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dibromide (1,2-dibromoethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dibromide (1,2-dibromoethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChlorobenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChlorobenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChlorobenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylbenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylbenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylbenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalXylenes (isomer & mixtures)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalXylenes (isomer & mixtures)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalXylenes (isomer & mixtures)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Totalo-Xylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Totalo-Xylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Totalo-Xylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalStyrene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalFuel InputRateFuel TypeUnits ofMeasureMeasurementMethodFuel InputRateFuel TypeTotal HeatInput(mmBtu/hr)Flue GasCO2(%)Flue GasMoisture (%)Flue GasTemperature (F)Flue GasO2(%)Flue Gas FlowRate (dscfm)Fuel #1Fue800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous800.05 12.5 12.6 6.5 192,598191.9 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous796.6 12.4 12.6 6.5 190,870190.3 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminous802.58.9 12.6 6.5 194,970191.9 27.76 bituminousEIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl isobutyl ketone (hexone)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,1,2-Trichloroethane14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,1,2-Trichloroethane24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,1,2-Trichloroethane34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalToluene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalToluene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalToluene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTetrachloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTetrachloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTetrachloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dibromide (1,2-dibromoethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dibromide (1,2-dibromoethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dibromide (1,2-dibromoethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChlorobenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChlorobenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChlorobenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylbenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylbenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylbenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalXylenes (isomer & mixtures)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalXylenes (isomer & mixtures)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalXylenes (isomer & mixtures)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Totalo-Xylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Totalo-Xylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Totalo-Xylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalStyrene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalUnits ofMeasureMeasurementMethodFuel InputRateFuel TypeUnits ofMeasureMeasurementMethodFuel Input Rate Fuel TypeUnits ofMeasureMeasurementMethodFuel #4el #2Fuel #3EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl isobutyl ketone (hexone)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,1,2-Trichloroethane14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,1,2-Trichloroethane24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,1,2-Trichloroethane34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalToluene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalToluene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalToluene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTetrachloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTetrachloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTetrachloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dibromide (1,2-dibromoethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dibromide (1,2-dibromoethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dibromide (1,2-dibromoethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChlorobenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChlorobenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChlorobenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylbenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylbenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylbenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalXylenes (isomer & mixtures)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalXylenes (isomer & mixtures)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalXylenes (isomer & mixtures)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Totalo-Xylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Totalo-Xylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Totalo-Xylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalStyrene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalSet a Set b Set c Set dRun No.μgμgμgμgOther Supporting InformationMethyl isobutyl ketone (hexone)2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Methyl isobutyl ketone (hexone)3T1 < 0.010 < 0.010 < 0.010 < 0.010Methyl isobutyl ketone (hexone)3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Methyl isobutyl ketone (hexone)3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <1,1,2-Trichloroethane1T1 < 0.010 < 0.010 < 0.010 < 0.0101,1,2-Trichloroethane1T2/ANA < 0.010 < 0.010 < 0.010 < 0.0101,1,2-Trichloroethane1TOTAL < 0.020 < 0.020 < 0.020 < 0.0201,1,2-Trichloroethane2T1 < 0.010 < 0.010 < 0.010 < 0.0101,1,2-Trichloroethane2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <1,1,2-Trichloroethane2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <1,1,2-Trichloroethane3T1 < 0.010 < 0.010 < 0.010 < 0.0101,1,2-Trichloroethane3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <1,1,2-Trichloroethane3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Toluene1T1 0.035 0.041 0.032 0.070Toluene1T2/ANA 0.024 0.027 < 0.010 < 0.010Toluene1TOTAL 0.059 0.068 < 0.042 < 0.080Toluene2T1 0.029 0.043 0.041 0.037Toluene2T2/ANA 0.014 0.103 0.051 0.027 <Toluene2TOTAL 0.043 0.146 0.092 0.064 <Toluene3T1 0.039 0.015 0.013 < 0.010Toluene3T2/ANA 0.016 < 0.010 < 0.010 < 0.010 <Toluene3TOTAL 0.055 < 0.025 < 0.023 < 0.020 <Tetrachloroethylene1T1 < 0.010 < 0.010 < 0.010 0.036Tetrachloroethylene1T2/ANA < 0.010 < 0.010 < 0.010 1.140Tetrachloroethylene1TOTAL < 0.020 < 0.020 < 0.020 1.176Tetrachloroethylene2T1 0.024 0.022 0.019 0.021Tetrachloroethylene2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Tetrachloroethylene2TOTAL < 0.034 < 0.032 < 0.029 < 0.031 <Tetrachloroethylene3T1 0.014 < 0.010 0.010 0.011Tetrachloroethylene3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Tetrachloroethylene3TOTAL < 0.024 < 0.020 < 0.020 < 0.021 <Ethylene dibromide (1,2-dibromoethan1T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylene dibromide (1,2-dibromoethan1T2/ANA < 0.010 < 0.010 < 0.010 < 0.010Ethylene dibromide (1,2-dibromoethan1TOTAL < 0.020 < 0.020 < 0.020 < 0.020Ethylene dibromide (1,2-dibromoethan2T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylene dibromide (1,2-dibromoethan2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Ethylene dibromide (1,2-dibromoethan2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Ethylene dibromide (1,2-dibromoethan3T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylene dibromide (1,2-dibromoethan3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Ethylene dibromide (1,2-dibromoethan3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Chlorobenzene1T1 < 0.010 < 0.010 < 0.010 < 0.010Chlorobenzene1T2/ANA < 0.010 < 0.010 < 0.010 < 0.010Chlorobenzene1TOTAL < 0.020 < 0.020 < 0.020 < 0.020Chlorobenzene2T1 < 0.010 < 0.010 < 0.010 < 0.010Chlorobenzene2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Chlorobenzene2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Chlorobenzene3T1 < 0.010 < 0.010 < 0.010 < 0.010Chlorobenzene3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Chlorobenzene3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Ethylbenzene1T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylbenzene1T2/ANA < 0.010 < 0.010 < 0.010 < 0.010Ethylbenzene1TOTAL < 0.020 < 0.020 < 0.020 < 0.020Ethylbenzene2T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylbenzene2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Ethylbenzene2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Ethylbenzene3T1 < 0.010 < 0.010 < 0.010 < 0.010Ethylbenzene3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <Ethylbenzene3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Xylenes (isomer & mixtures)1T1 < 0.030 < 0.030 < 0.030 < 0.030Xylenes (isomer & mixtures)1T2/ANA < 0.030 < 0.030 < 0.030 < 0.030Xylenes (isomer & mixtures)1TOTAL < 0.060 < 0.060 < 0.060 < 0.060Xylenes (isomer & mixtures)2T1 < 0.030 < 0.030 < 0.030 < 0.030Xylenes (isomer & mixtures)2T2/ANA < 0.030 < 0.030 < 0.030 < 0.030 <Xylenes (isomer & mixtures)2TOTAL < 0.060 < 0.060 < 0.060 < 0.060 <Xylenes (isomer & mixtures)3T1 < 0.030 < 0.030 < 0.030 < 0.030Xylenes (isomer & mixtures)3T2/ANA < 0.030 < 0.030 < 0.030 < 0.030 <Xylenes (isomer & mixtures)3TOTAL < 0.060 < 0.060 < 0.060 < 0.060 <o-Xylene1T1 < 0.010 < 0.010 < 0.010 < 0.010o-Xylene1T2/ANA < 0.010 < 0.010 < 0.010 < 0.010o-Xylene1TOTAL < 0.020 < 0.020 < 0.020 < 0.020o-Xylene2T1 < 0.010 < 0.010 < 0.010 < 0.010o-Xylene2T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <o-Xylene2TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <o-Xylene3T1 < 0.010 < 0.010 < 0.010 < 0.010o-Xylene3T2/ANA < 0.010 < 0.010 < 0.010 < 0.010 <o-Xylene3TOTAL < 0.020 < 0.020 < 0.020 < 0.020 <Styrene1T1 < 0.010 < 0.010 < 0.010 < 0.010Styrene1T2/ANA < 0.010 < 0.010 < 0.010 0.016Styrene1TOTAL < 0.020 < 0.020 < 0.020 < 0.026EIA Facility CodeFacility Name Boiler ID10774 Southampton Pow1_2Speciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the totalFractionCompound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End Date Test End TimeMethyl isobutyl ketone (hexone)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalMethyl isobutyl ketone (hexone)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Methyl isobutyl ketone (hexone)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total1,1,2-Trichloroethane14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**1,1,2-Trichloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total1,1,2-Trichloroethane24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**1,1,2-Trichloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total1,1,2-Trichloroethane34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**1,1,2-Trichloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalToluene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Toluene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalToluene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Toluene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalToluene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Toluene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalTetrachloroethylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Tetrachloroethylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalTetrachloroethylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Tetrachloroethylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalTetrachloroethylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Tetrachloroethylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylene dibromide (1,2-dibromoethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylene dibromide (1,2-dibromoethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylene dibromide (1,2-dibromoethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylene dibromide (1,2-dibromoethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylene dibromide (1,2-dibromoethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylene dibromide (1,2-dibromoethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalChlorobenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Chlorobenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalChlorobenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Chlorobenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalChlorobenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Chlorobenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalEthylbenzene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Ethylbenzene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalEthylbenzene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Ethylbenzene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalEthylbenzene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Ethylbenzene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalXylenes (isomer & mixtures)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Xylenes (isomer & mixtures)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalXylenes (isomer & mixtures)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**Xylenes (isomer & mixtures)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM TotalXylenes (isomer & mixtures)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**Xylenes (isomer & mixtures)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Totalo-Xylene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**o-Xylene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Totalo-Xylene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half*o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half**o-Xylene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Totalo-Xylene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half*o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half**o-Xylene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM TotalStyrene14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half*Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half**Styrene1 4/28/2010 9:48 AM 4/28/2010 12:07 PM TotalCondTotalTotalμgμgRun No.Set aSet b Set c Set d dsLSample Volume (dsL)0.800 < 0.880 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.800 < 0.840 ND320.3420.23 20.16 20.11 80.83< 0.020.800 < 0.880 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.040119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.080119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------0.178119.5420.57 20.56 20.54 81.20------< 0.071119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.249119.5420.57 20.56 20.5481.20< 0.02------0.150220.4720.32 20.34 20.22 81.35------0.020 < 0.215220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.365220.4720.32 20.34 20.2281.35< 0.02------ < 0.077320.3420.23 20.16 20.11 80.83------0.020 < 0.066320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.143320.3420.23 20.16 20.1180.83< 0.02------ < 0.066119.5420.57 20.56 20.54 81.20------< 1.170119.5420.57 20.56 20.54 81.20< 0.020.000 < 1.236119.5420.57 20.56 20.5481.20< 0.02------0.086220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.146220.4720.32 20.34 20.2281.35< 0.02------ < 0.045320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.105320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.040119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.080119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.040119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.080119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.040119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.080119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.120 ND119.5420.57 20.56 20.54 81.20------< 0.120119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.240119.5420.57 20.56 20.5481.20< 0.02------ < 0.120 ND220.4720.32 20.34 20.22 81.35------0.040 < 0.160 ND220.4720.32 20.34 20.22 81.35< 0.020.040 < 0.280 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.120 ND320.3420.23 20.16 20.11 80.83------0.040 < 0.160 ND320.3420.23 20.16 20.11 80.83< 0.020.040 < 0.280 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.040119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.080119.5420.57 20.56 20.5481.20< 0.02------ < 0.040 ND220.4720.32 20.34 20.22 81.35------0.020 < 0.060 ND220.4720.32 20.34 20.22 81.35< 0.020.020 < 0.100 ND220.4720.32 20.34 20.2281.35< 0.02------ < 0.040 ND320.3420.23 20.16 20.11 80.83------0.020 < 0.060 ND320.3420.23 20.16 20.11 80.83< 0.020.020 < 0.100 ND320.3420.23 20.16 20.1180.83< 0.02------ < 0.040 ND119.5420.57 20.56 20.54 81.20------< 0.046119.5420.57 20.56 20.54 81.20< 0.020.000 < 0.086119.5420.57 20.56 20.5481.20< 0.02EIA Facility CodeFacility Name Boiler IDs:10774 Southampton Pow1_2* Front half fraction contains first Tenax tube results** Back half fraction contains second Tenax and Anasorb tube resultsSpeciated Volatile Organic HAP Emission DataNote: Each run should include a value for each fraction and the total for each pollutant.FractionMeasuredValue(μg/m3)BasisTest Method UsedData Flag (ADL,BDL, DDL)Test MethodCommentslb/mmBtu μg/dscm @ 7% O2Compound(use drop down to define for as manyrows as needed)Run Number Test Start Date Test Start Time Test End DateVolatile Organic HAP Emission Test ResultsTest End TimeCalculated Emission RateSteam Output(1000 lb/hr)Styrene24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Styrene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Styrene2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Styrene34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Styrene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Styrene3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546Bromoform (tribromomethane)14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.5Bromoform (tribromomethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.37E-07][<0.48]545.5Bromoform (tribromomethane)1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.73E-07][<0.95]545.5Bromoform (tribromomethane)24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.5Bromoform (tribromomethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.5Bromoform (tribromomethane)2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.5Bromoform (tribromomethane)34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]546Bromoform (tribromomethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]546Bromoform (tribromomethane)3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]5461, 1, 2, 2-Tetrachloroethane14/28/2010 9:48 AM 4/28/2010 12:07 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.37E-07][<0.48]545.51, 1, 2, 2-Tetrachloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Back Half** [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<4.37E-07][<0.48]545.51, 1, 2, 2-Tetrachloroethane1 4/28/2010 9:48 AM 4/28/2010 12:07 PM Total[<0.99] Dry U.S. EPA Method 0031 with SW-846 Method 8260BDLLFor M0031 we are report[<8.73E-07][<0.95]545.51, 1, 2, 2-Tetrachloroethane24/28/2010 12:45 PM 4/28/2010 3:08 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.36E-07][<0.47]545.51, 1, 2, 2-Tetrachloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.54E-07][<0.71]545.51, 1, 2, 2-Tetrachloroethane2 4/28/2010 12:45 PM 4/28/2010 3:08 PM Total[<1.23] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.09E-06][<1.19]545.51, 1, 2, 2-Tetrachloroethane34/28/2010 3:40 PM 4/28/2010 5:51 PMFront Half* [<0.49] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<4.39E-07][<0.48]5461, 1, 2, 2-Tetrachloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Back Half** [<0.74] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<6.58E-07][<0.72]5461, 1, 2, 2-Tetrachloroethane3 4/28/2010 3:40 PM 4/28/2010 5:51 PM Total[<1.24] Dry U.S. EPA Method 0031 with SW-846 Method 8260BBDLFor M0031 we are report[<1.10E-06][<1.19]546