Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

4042 4042 Wisconsin Electric Power Company Wisconsin Electric Power Company legal owner231 West Michigan Avenue Milwaukee WI 53203

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

Valley 1035 West Canal Street Milwaukee WI 53233 1035 West Canal Street Milwaukee WI 53233

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

TRUE FALSE TRUE FALSE TRUE TRUE FALSE TRUE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE TRUE (1) Submit the results of monitoring or a summary No EPA - Region V; Clean Air Markets Division ~~~~~~~ BOILER INFORMATION ~~~~~~~(1) Design and opera of monitoring results required by this permit to the De

Page 4
Facility_Information

N ~~~~~~~(1) Design and operating steam temperature should be 900 degF for all four boilers.(2) Capacity factor under the "Boiler I

Page 5
Facility_Information

2) Capacity factor under the "Boiler Information" tab is based on turbine generation.(3) The plant uses combustion optimization software t

Page 6
Facility_Information

s combustion optimization software to optimize the performance of the low Nox burners and over-fired air systems.~~~~~~~ PERMIT

Page 7
Facility_Information

ir systems.~~~~~~~ PERMITTED EMISSION LIMIT ~~~~~~~PM:1) There is no pollutant selection for TOTAL PM, therefore, t

Page 8
Facility_Information

selection for TOTAL PM, therefore, the polluntant chosen was filterable PM, with a permitted emission rate of 0.15 pounds per million Btu he

Page 9
Facility_Information

ate of 0.15 pounds per million Btu heat input [WDNR NR415]2) Consent decree (03-C-0371) limit entered on October 1, 20073) A

Page 10
Facility_Information

tered on October 1, 20073) Additional Pollutant Limits:(a) Concentrations of the followings NR 445 compounds in the cleaning wa

Page 11
Facility_Information

R 445 compounds in the cleaning wastes may not be more than the following (see below for specific permit details): Ca: 1905 mg/l Sn

Page 12
Facility_Information

mit details): Ca: 1905 mg/l Sn: 657 mg/l Hg: 133 mg/l4) HAP Permit Limits:(2) Boilers B21, B22, B23 and B24 may incin

Page 13
Facility_Information

rs B21, B22, B23 and B24 may incinerate boiler chemical cleaning waste liquids with the following conditions:(

Page 14
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

4042 3 Air Quality Manager Terry Coughlin 4142212293 terry.coughlin@we-energies.com TRUE

4042 4 Sr EnvironmSteve Stretchberry ental Engineer 4142212174 steve.stretchberry FALSE@we-energies.com

Page 15
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

4042 bituminous 100 100

Page 16
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

Page 17
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

4042 Boiler cleaning solutions TRUE TRUE 26586 number/yearValley Boiler-2 64,632 gallons burned in VB-4 06/13 to 0No CAA Section 129 requirements are 

4042 Propane TRUE TRUE 3599 number/yearOn average over the past 5 y No CAA Section 129 requirements are ears, the Valley has burned 3

Page 18
facility_other_materials

rcra_explain

CAA Section 129 requirements are cost-prohibitive

CAA Section 129 requirements are cost-prohibitive

Page 19
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

4042 1 Wall firing - front firing Wet Bottomcoal 796 868 72

4042 2 Wall firing - front firing Wet Bottomcoal 796 868 72

4042 3 Wall firing - front firing Wet Bottomcoal 796 868 72

4042 4 Wall firing - front firing Wet Bottomcoal 796 868 72

Page 20
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

70 89.3 87.4 1600 1540 1 1 FALSE

70 89.3 87.4 1600 1540 1 1 FALSE

70 89.3 87.3 1600 1540 1 1 FALSE

70 89.3 87.7 1600 1540 1 1 FALSE

Page 21
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 8157 49 N FALSE

FALSE 8066 49 N FALSE

FALSE 7737 42 N FALSE

FALSE 7734 42 N FALSE

Page 22
boiler_information

NOx_controlSO2_controlcombustion_additives

Yes Yes No

Yes Yes No

Yes Yes No

Yes Yes No

Page 23
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

4042 1 coal - bituminous2007 99.9

4042 1 coal - bituminous2008 99.8

4042 1 coal - bituminous2009 99.8

4042 1 natural gas 2007 0.1

4042 1 natural gas 2008 0.2

4042 1 natural gas 2009 0.2

4042 1 other fossil fuel (specify 2007 ) 0 propane

4042 1 other fossil fuel (specify 2008 ) 0 propane

4042 1 other fossil fuel (specify 2009 ) 0 propane

4042 2 coal - bituminous2007 99.9

4042 2 coal - bituminous2008 99.8

4042 2 coal - bituminous2009 99.8

4042 2 natural gas 2007 0.1

4042 2 natural gas 2008 0.2

4042 2 natural gas 2009 0.2

4042 2 other fossil fuel (specify 2007 ) 0 propane

4042 2 other fossil fuel (specify 2008 ) 0 propane

4042 2 other fossil fuel (specify 2009 ) 0 propane

4042 3 coal - bituminous2007 99.8

4042 3 coal - bituminous2008 99.7

4042 3 coal - bituminous2009 99.7

4042 3 natural gas 2007 0.2

4042 3 natural gas 2008 0.3

4042 3 natural gas 2009 0.3

4042 3 other fossil fuel (specify 2007 ) 0 propane

4042 3 other fossil fuel (specify 2008 ) 0 propane

4042 3 other fossil fuel (specify 2009 ) 0 propane

4042 4 coal - bituminous2007 99.8

4042 4 coal - bituminous2008 99.8

4042 4 coal - bituminous2009 99.8

4042 4 natural gas 2007 0.2

4042 4 natural gas 2008 0.2

4042 4 natural gas 2009 0.2

4042 4 other fossil fuel (specify 2007 ) 0 propane

4042 4 other fossil fuel (specify 2008 ) 0 propane

4042 4 other fossil fuel (specify 2009 ) 0 propane

Page 24
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

4042 1 Low NOx Burner 6/1/2008

4042 1 Overfire Air 6/1/2008

4042 2 Low NOx Burner 6/1/2008

4042 2 Overfire Air 6/1/2008

4042 3 Low NOx Burner 10/1/2008

4042 3 Overfire Air 10/1/2008

4042 4 Low NOx Burner 10/1/2008

4042 4 Overfire Air 10/1/2008

Page 25
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

4042 1 Low Sulfur Coal 6/1/1999

4042 2 Low Sulfur Coal 6/1/1999

4042 3 Low Sulfur Coal 6/1/1999

4042 4 Low Sulfur Coal 6/1/1999

Page 26
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

Page 27
facility_units

facility_id unit_id

4042 1

4042 2

Page 28
unit_boilers

facility_id unit_id boiler_id

4042 1 1

4042 1 2

4042 2 3

4042 2 4

Page 29
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

4042 VAPP-PM-B1PM control Fabric Filter, pulse FALSE 6/1/1994

4042 VAPP-PM-B2PM control Fabric Filter, pulse FALSE 6/1/1994

4042 VAPP-PM-B3PM control Fabric Filter, pulse FALSE 6/1/1995

4042 VAPP-PM-B4PM control Fabric Filter, pulse FALSE 6/1/1995

Page 30
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

Page 31
facility_sampling_ports

facility_id sampling_port_id

4042 VAPP-SP-B1

4042 VAPP-SP-B2

4042 VAPP-SP-B3

4042 VAPP-SP-B4

4042 VAPP-SP-BH1

4042 VAPP-SP-BH2

4042 VAPP-SP-BH3

4042 VAPP-SP-BH4

4042 VAPP-SP-S11

4042 VAPP-SP-S12

Page 32
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

4042 VAPP-S11 400 11 59.15

4042 VAPP-S12 400 11 56.79

Page 33
configurations

facility_id configuration_id

4042 VAPP-B1

4042 VAPP-B2

4042 VAPP-B3

4042 VAPP-B4

Page 34
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

4042 VAPP-B1 1 1 Unit

4042 VAPP-B1 VAPP-PM-B1 3 PM control

4042 VAPP-B1 VAPP-S11 6 Stack

4042 VAPP-B1 VAPP-SP-B1 2 Sampling Port pevious

4042 VAPP-B1 VAPP-SP-BH1 4 Sampling Port pevious

4042 VAPP-B1 VAPP-SP-S11 5 Sampling Port next

4042 VAPP-B2 1 1 Unit

4042 VAPP-B2 VAPP-PM-B2 3 PM control

4042 VAPP-B2 VAPP-S11 6 Stack

4042 VAPP-B2 VAPP-SP-B2 2 Sampling Port pevious

4042 VAPP-B2 VAPP-SP-BH2 4 Sampling Port pevious

4042 VAPP-B2 VAPP-SP-S11 5 Sampling Port next

4042 VAPP-B3 2 1 Unit

4042 VAPP-B3 VAPP-PM-B3 3 PM control

4042 VAPP-B3 VAPP-S12 6 Stack

4042 VAPP-B3 VAPP-SP-B3 2 Sampling Port pevious

4042 VAPP-B3 VAPP-SP-BH3 4 Sampling Port pevious

4042 VAPP-B3 VAPP-SP-S12 5 Sampling Port next

4042 VAPP-B4 2 1 Unit

4042 VAPP-B4 VAPP-PM-B4 3 PM control

4042 VAPP-B4 VAPP-S12 6 Stack

4042 VAPP-B4 VAPP-SP-B4 2 Sampling Port pevious

4042 VAPP-B4 VAPP-SP-BH4 4 Sampling Port pevious

4042 VAPP-B4 VAPP-SP-S12 5 Sampling Port next

Page 35
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

4042 VAPP-B1 PM (Filterable) Fderal - Title V Operating Permit 0.15 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.03 pound per million British Thermal U

4042 VAPP-B1 Sulfur Dioxide (SO2) Federal - Title V Operating Permit 3.28 pound per million British Thermal Unit (lb/MMBtu) 24 hours

4042 VAPP-B1 Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.28 pound per million British Thermal Unit (lb/MMBtu) 30 days

4042 VAPP-B2 PM (Filterable) Fderal - Federal Operating Permit 0.15 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.03 pound per million British Thermal U

4042 VAPP-B2 Nitrogen Oxide (NOx) Federal - Federal Operating Permit 0.28 pound per million British Thermal Unit (lb/MMBtu) 30 days

4042 VAPP-B2 Sulfur Dioxide (SO2) Federal - Federal Operating Permit 3.28 pound per million British Thermal Unit (lb/MMBtu) 24 hours 0.1 pound per million British Thermal U

4042 VAPP-B3 PM (Filterable) Fderal - Federal Operating Permit 0.15 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.03 pound per million British Thermal U

4042 VAPP-B3 Nitrogen Oxide (NOx) Federal - Federal Operating Permit 0.28 pound per million British Thermal Unit (lb/MMBtu) 30 days

4042 VAPP-B3 Sulfur Dioxide (SO2) Federal - Federal Operating Permit 3.28 pound per million British Thermal Unit (lb/MMBtu) 24 hours 0.1 pound per million British Thermal U

4042 VAPP-B4 PM (Filterable) Fderal - Federal Operating Permit 0.15 pound per million British Thermal Unit (lb/MMBtu) 3 hours 0.03 pound per hour (lb/hr)

4042 VAPP-B4 Nitrogen Oxide (NOx) Federal - Federal Operating Permit 0.28 pound per million British Thermal Unit (lb/MMBtu) 30 days

4042 VAPP-B4 Sulfur Dioxide (SO2) Federal - Federal Operating Permit 3.28 pound per million British Thermal Unit (lb/MMBtu) 24 hours 0.1 pound per million British Thermal U

Page 36
configuration_pollutants1

avg_period_2emlimit_details test_methodemrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping

3 hours (1) The permittee may EPA-RTM 5 and 202 not cause, allow or permit the emission of particulate matter to the ambient air from any 0.015 pound per million British Thermal Unit (lb/MMBtu) No (c)(1) Whenever particulate matter testing is(c)(2) The permittee shall retain co stac

1) averaged over any 24-hour period in amountsgreater than 3.28 poundsper million Btu heatinput. [s. (b)(1) The permittee shall calibrate, maintain a(1) Unless otherwise provided, the 

(f) 0.28 pounds per million Btu of heat input on a 30-day 0.21 pound per million British Thermal Unit (lb/MMBtu) No rollingaverage basis, on or after December31, 2007(b)(1) The permittee shall calibrate, maintain a(c)(3) The permittee shall keep on 

3 hours (1) The permittee may EPA-RTM 5 and 202 not cause, allow or permit the emission of particulate matter to the ambient air from any 0.015 pound per million British Thermal Unit (lb/MMBtu) No (c)(1) Whenever particulate matter testing is(c)(2) The permittee shall retain co stac

(f) 0.28 pounds per million Btu of heat input on a 30-day 0.21 pound per million British Thermal Unit (lb/MMBtu) No rollingaverage basis, on or after December31, 2007(b)(1) The permittee shall calibrate, maintain a(c)(3) The permittee shall keep on 

30 days 1) averaged over any 24-hour period in amountsgreater than 3.28 poundsper million Btu heatinput. [s. (b)(1) The permittee shall calibrate, maintain a(1) Unless otherwise provided, the 

3 hours (1) The permittee may EPA-RTM 5 and 202 not cause, allow or permit the emission of particulate matter to the ambient air from any 0.015 pound per million British Thermal Unit (lb/MMBtu) No (c)(1) Whenever particulate matter testing is(c)(2) The permittee shall retain co stac

0.21 pound per million British Thermal Unit (lb/MMBtu) No (b)(1) The permittee shall calibrate, maintain a(c)(3) The permittee shall keep on 

30 days 1) averaged over any 24-hour period in amountsgreater than 3.28 poundsper million Btu heatinput. [s. (b)(1) The permittee shall calibrate, maintain a(1) Unless otherwise provided, the 

3 hours (1) The permittee may EPA-RTM 5 and 202 not cause, allow or permit the emission of particulate matter to the ambient air from any 0.015 pound per million British Thermal Unit (lb/MMBtu) No (c)(1) Whenever particulate matter testing is(c)(2) The permittee shall retain co stac

0.21 pound per million British Thermal Unit (lb/MMBtu) No (b)(1) The permittee shall calibrate, maintain a(c)(3) The permittee shall keep on 

30 days 1) averaged over any 24-hour period in amountsgreater than 3.28 poundsper million Btu heatinput. [s. (b)(1) The permittee shall calibrate, maintain a(1) Unless otherwise provided, the 

Page 37
configuration_pollutants1

req_reporting

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(c)(3) The permittee shall submit excess emission reports to the Department according to either of the following. (a) Quarterly w

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(c)(3) The permittee shall submit excess emission reports to the Department according to either of the following. (a) Quarterly w

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(c)(3) The permittee shall submit excess emission reports to the Department according to either of the following. (a) Quarterly w

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(1) Submit the results of monitoring or a summary of monitoring results required by this permit to the Department every 6 mont

(c)(3) The permittee shall submit excess emission reports to the Department according to either of the following. (a) Quarterly w

Page 38
configuration_pollutants1

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

either of the following. (a) Quarterly within 30 days following the end of each calendar quarter; or (b) In accordance with a cooperative agree

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

either of the following. (a) Quarterly within 30 days following the end of each calendar quarter; or (b) In accordance with a cooperative agree

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

either of the following. (a) Quarterly within 30 days following the end of each calendar quarter; or (b) In accordance with a cooperative agree

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

rmit to the Department every 6 months.(a) The time periods to be addressed by the submittal are: January 1 to June 30 and July 1 to Dec

either of the following. (a) Quarterly within 30 days following the end of each calendar quarter; or (b) In accordance with a cooperative agree

Page 39
configuration_pollutants1

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

ccordance with a cooperative agreement9 [s. NR 439.09(10), Wis. Adm. Code] (c)(6) The excess emission reports required by condition I.A

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

ccordance with a cooperative agreement9 [s. NR 439.09(10), Wis. Adm. Code] (c)(6) The excess emission reports required by condition I.A

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

ccordance with a cooperative agreement9 [s. NR 439.09(10), Wis. Adm. Code] (c)(6) The excess emission reports required by condition I.A

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

nuary 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisconsin Department of Natural Resources, Sou

ccordance with a cooperative agreement9 [s. NR 439.09(10), Wis. Adm. Code] (c)(6) The excess emission reports required by condition I.A

Page 40
configuration_pollutants1

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

sion reports required by condition I.A.3.c.(3) shall contain the information in condition I.E.2.a.(1). [s. NR 439.09(10)(a), Wis. Adm. Code]

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

sion reports required by condition I.A.3.c.(3) shall contain the information in condition I.E.2.a.(1). [s. NR 439.09(10)(a), Wis. Adm. Code]

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

sion reports required by condition I.A.3.c.(3) shall contain the information in condition I.E.2.a.(1). [s. NR 439.09(10)(a), Wis. Adm. Code]

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

epartment of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, pho

sion reports required by condition I.A.3.c.(3) shall contain the information in condition I.E.2.a.(1). [s. NR 439.09(10)(a), Wis. Adm. Code]

Page 41
configuration_pollutants1

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

 439.09(10)(a), Wis. Adm. Code]REPORTING:(1) Submit the results of monitoring or a summary of monitoring results required by 

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

 439.09(10)(a), Wis. Adm. Code]REPORTING:(1) Submit the results of monitoring or a summary of monitoring results required by 

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

 439.09(10)(a), Wis. Adm. Code]REPORTING:(1) Submit the results of monitoring or a summary of monitoring results required by 

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

ng Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each reporting period, or in accordance with a coopera

 439.09(10)(a), Wis. Adm. Code]REPORTING:(1) Submit the results of monitoring or a summary of monitoring results required by 

Page 42
configuration_pollutants1

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

ary of monitoring results required by this permit to the Department every 6 months.(a) The time periods to be addressed by the submittal 

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

ary of monitoring results required by this permit to the Department every 6 months.(a) The time periods to be addressed by the submittal 

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

ary of monitoring results required by this permit to the Department every 6 months.(a) The time periods to be addressed by the submittal 

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

riod, or in accordance with a cooperative agreement20.(c) All deviations from and violations of applicable requirements shall be clearly id

ary of monitoring results required by this permit to the Department every 6 months.(a) The time periods to be addressed by the submittal 

Page 43
configuration_pollutants1

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

ods to be addressed by the submittal are: January 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisco

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

ods to be addressed by the submittal are: January 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisco

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

ods to be addressed by the submittal are: January 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisco

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

able requirements shall be clearly identified in the submittal.(d) Each submittal shall be certified by a responsible official as to the truth, a

ods to be addressed by the submittal are: January 1 to June 30 and July 1 to December 31.(b) The report shall be submitted to the Wisco

Page 44
configuration_pollutants1

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

eport shall be submitted to the Wisconsin Department of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Lu

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

eport shall be submitted to the Wisconsin Department of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Lu

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

eport shall be submitted to the Wisconsin Department of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Lu

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

 responsible official as to the truth, accuracy and completeness of the report. [s. NR 439.03(1)(b), Wis. Adm. Code](2) Submit a certificat

eport shall be submitted to the Wisconsin Department of Natural Resources, Southeast Region Air Management Program, 2300 N. Martin Lu

Page 45
configuration_pollutants1

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

agement Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each repor

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

agement Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each repor

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

agement Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each repor

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

Adm. Code](2) Submit a certification of compliance with the requirements of this permit to the Department and U.S. EPA annually.(a) 

agement Program, 2300 N. Martin Luther King Drive, Milwaukee, WI 53212, phone (414)263-8500 within 60 days after the end of each repor

Page 46
configuration_pollutants1

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

n 60 days after the end of each reporting period, or in accordance with a cooperative agreement20.(c) All deviations from and 

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

n 60 days after the end of each reporting period, or in accordance with a cooperative agreement20.(c) All deviations from and 

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

n 60 days after the end of each reporting period, or in accordance with a cooperative agreement20.(c) All deviations from and 

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

tment and U.S. EPA annually.(a) The time period to be addressed by the report is the January 1 to December 31 perio

n 60 days after the end of each reporting period, or in accordance with a cooperative agreement20.(c) All deviations from and 

Page 47
configuration_pollutants1

ecember 31 perio

c) All deviations from and 

ecember 31 perio

ecember 31 perio

ecember 31 perio

c) All deviations from and 

ecember 31 perio

ecember 31 perio

c) All deviations from and 

ecember 31 perio

ecember 31 perio

c) All deviations from and 

Page 48
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

Page 49
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

Page 50
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

Page 51
control_technologies

feed_rate_units

Page 52
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

Page 53
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

Page 54
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

Page 55
control_costs

CBI

Page 56
misc_controls

facility_id misc_control_id control_description

Page 57
misc_control_configurations

facility_id misc_control_id configuration_id

Page 58
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

4042 VAPP-COMP-01 1/1/2009 56795 short tons (2000 lbs) coal CO

4042 VAPP-COMP-02 2/1/2009 66458 short tons (2000 lbs) coal CO

4042 VAPP-COMP-03 3/1/2009 72202 short tons (2000 lbs) coal CO

4042 VAPP-COMP-04 4/1/2009 54628 short tons (2000 lbs) coal CO

4042 VAPP-COMP-05 5/1/2009 37911 short tons (2000 lbs) coal CO

4042 VAPP-COMP-06 6/1/2009 33095 short tons (2000 lbs) coal CO

4042 VAPP-COMP-07 7/1/2009 44400 short tons (2000 lbs) coal CO

4042 VAPP-COMP-08 8/1/2009 32976 short tons (2000 lbs) coal CO

4042 VAPP-COMP-09 9/1/2009 39262 short tons (2000 lbs) coal CO

4042 VAPP-COMP-10 10/1/2009 52471 short tons (2000 lbs) coal CO

4042 VAPP-COMP-11 11/1/2009 43828 short tons (2000 lbs) coal CO

4042 VAPP-COMP-12 12/1/2009 77802 short tons (2000 lbs) coal CO

4042 VAPP-HAP-013/1/2009 195454 short tons (2000 lbs) coal CO

4042 VAPP-HAP-026/1/2009 125634 short tons (2000 lbs) coal CO

4042 VAPP-HAP-039/1/2009 116637 short tons (2000 lbs) coal CO

4042 VAPP-HAP-0412/1/2009 174102 short tons (2000 lbs) coal CO

Page 59
fuel_shipments

coal_seam shipment_method

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Barge

Page 60
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

4042 VAPP-COMP-01 VAPP-B1

4042 VAPP-COMP-01 VAPP-B2

4042 VAPP-COMP-01 VAPP-B3

4042 VAPP-COMP-01 VAPP-B4

4042 VAPP-COMP-02 VAPP-B1

4042 VAPP-COMP-02 VAPP-B2

4042 VAPP-COMP-02 VAPP-B3

4042 VAPP-COMP-02 VAPP-B4

4042 VAPP-COMP-03 VAPP-B1

4042 VAPP-COMP-03 VAPP-B2

4042 VAPP-COMP-03 VAPP-B3

4042 VAPP-COMP-03 VAPP-B4

4042 VAPP-COMP-04 VAPP-B1

4042 VAPP-COMP-04 VAPP-B2

4042 VAPP-COMP-04 VAPP-B3

4042 VAPP-COMP-04 VAPP-B4

4042 VAPP-COMP-05 VAPP-B1

4042 VAPP-COMP-05 VAPP-B2

4042 VAPP-COMP-05 VAPP-B3

4042 VAPP-COMP-05 VAPP-B4

4042 VAPP-COMP-06 VAPP-B1

4042 VAPP-COMP-06 VAPP-B2

4042 VAPP-COMP-06 VAPP-B3

4042 VAPP-COMP-06 VAPP-B4

4042 VAPP-COMP-07 VAPP-B1

4042 VAPP-COMP-07 VAPP-B2

4042 VAPP-COMP-07 VAPP-B3

4042 VAPP-COMP-07 VAPP-B4

4042 VAPP-COMP-08 VAPP-B1

4042 VAPP-COMP-08 VAPP-B2

4042 VAPP-COMP-08 VAPP-B3

4042 VAPP-COMP-08 VAPP-B4

4042 VAPP-COMP-09 VAPP-B1

4042 VAPP-COMP-09 VAPP-B2

4042 VAPP-COMP-09 VAPP-B3

4042 VAPP-COMP-09 VAPP-B4

4042 VAPP-COMP-10 VAPP-B1

4042 VAPP-COMP-10 VAPP-B2

4042 VAPP-COMP-10 VAPP-B3

4042 VAPP-COMP-10 VAPP-B4

4042 VAPP-COMP-11 VAPP-B1

4042 VAPP-COMP-11 VAPP-B2

4042 VAPP-COMP-11 VAPP-B3

4042 VAPP-COMP-11 VAPP-B4

4042 VAPP-COMP-12 VAPP-B1

4042 VAPP-COMP-12 VAPP-B2

4042 VAPP-COMP-12 VAPP-B3

4042 VAPP-COMP-12 VAPP-B4

4042 VAPP-HAP-01 VAPP-B1

4042 VAPP-HAP-01 VAPP-B2

4042 VAPP-HAP-01 VAPP-B3

Page 61
fuel_shipment_configurations

4042 VAPP-HAP-01 VAPP-B4

4042 VAPP-HAP-02 VAPP-B1

4042 VAPP-HAP-02 VAPP-B2

4042 VAPP-HAP-02 VAPP-B3

4042 VAPP-HAP-02 VAPP-B4

4042 VAPP-HAP-03 VAPP-B1

4042 VAPP-HAP-03 VAPP-B2

4042 VAPP-HAP-03 VAPP-B3

4042 VAPP-HAP-03 VAPP-B4

4042 VAPP-HAP-04 VAPP-B1

4042 VAPP-HAP-04 VAPP-B2

4042 VAPP-HAP-04 VAPP-B3

4042 VAPP-HAP-04 VAPP-B4

Page 62
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

4042 VAPP-COMP-01 COMP-01 56795 tons 0.48 10.01 12897 Btu/lb

4042 VAPP-COMP-02 COMP-02 66458 tons 0.5 10.57 12772 Btu/lb

4042 VAPP-COMP-03 COMP-03 72202 tons 0.49 10.39 12842 Btu/lb

4042 VAPP-COMP-04 COMP-04 54628 tons 0.47 10.51 12798 Btu/lb

4042 VAPP-COMP-05 COMP-05 37911 tons 0.53 10.51 12761 Btu/lb

4042 VAPP-COMP-06 COMP-06 33095 tons 0.5 10.3 12713 Btu/lb

4042 VAPP-COMP-07 COMP-07 44400 tons 0.51 10.22 12726 Btu/lb

4042 VAPP-COMP-08 COMP-08 32976 tons 0.51 10.54 12678 Btu/lb

4042 VAPP-COMP-09 COMP-09 39262 tons 0.48 10.36 12738 Btu/lb

4042 VAPP-COMP-10 COMP-10 52471 tons 0.52 8.44 13075 Btu/lb

4042 VAPP-COMP-11 COMP-11 43828 tons 0.5 9.72 12863 Btu/lb

4042 VAPP-COMP-12 COMP-12 77802 tons 0.5 8.91 13062 Btu/lb

4042 VAPP-HAP-01 HAP-01 195454 tons 0.48 10.25 12846 Btu/lb

4042 VAPP-HAP-02 HAP-02 125634 tons 0.51 10.54 12667 Btu/lb

4042 VAPP-HAP-03 HAP-03 116637 tons 0.53 10.35 12708 Btu/lb

4042 VAPP-HAP-04 HAP-04 174102 tons 0.49 9.02 12938 Btu/lb

Page 63
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

other (please specify Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

330 parts per million (dry97) (ppm) parts per million (dry other (please specify ) (ppm) Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

200 parts per million (dry82) (ppm) parts per million (dry other (please specify ) (ppm) Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

230 parts per million (dry86) (ppm) parts per million (dry other (please specify ) (ppm) Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

230 parts per million (dry88) (ppm) parts per million (dry other (please specify ) (ppm) Standard operating procedures, contractual obligations, permit requir) Other We Energies333 W Everett St

Page 64
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Milwaukee WI 53203 We Energies333 W Everett St Milwaukee WI 53203 No

Page 65
fuel_shipment_samples

analysis_copies

Page 66
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

4042 VAPP-COMP-01 COMP-01 Mercury (Hg) 0.024 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-02 COMP-02 Mercury (Hg) 0.023 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-03 COMP-03 Mercury (Hg) 0.028 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-04 COMP-04 Mercury (Hg) 0.018 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-05 COMP-05 Mercury (Hg) 0.034 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-06 COMP-06 Mercury (Hg) 0.018 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-07 COMP-07 Mercury (Hg) 0.027 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-08 COMP-08 Mercury (Hg) 0.028 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-09 COMP-09 Mercury (Hg) 0.036 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-10 COMP-10 Mercury (Hg) 0.027 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-11 COMP-11 Mercury (Hg) 0.024 parts per million (dry FALSE) (ppm)

4042 VAPP-COMP-12 COMP-12 Mercury (Hg) 0.018 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Antimony (Sb) 0.38 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Arsenic (As) 0.74 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Barium (Ba) 220 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Beryllium (Be) 0.61 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Cadmium (Cd) 0.2 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Chromium (Cr) 4.7 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Cobalt (Co) 1.5 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Copper (Cu) 8.7 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Lead (Pb) 5.3 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Manganese (Mn) 11 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Mercury (Hg) 0.018 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Nickel (Ni) 4.8 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Selenium (Se) 0.77 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-01 HAP-01 Vanadium (V) 13 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Antimony (Sb) 0.46 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Arsenic (As) 1.3 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Barium (Ba) 220 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Beryllium (Be) 0.7 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Cadmium (Cd) 0.14 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Chromium (Cr) 5.8 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Cobalt (Co) 1.7 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Copper (Cu) 10 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Lead (Pb) 5.9 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Manganese (Mn) 15 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Mercury (Hg) 0.02 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Nickel (Ni) 6 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Selenium (Se) 1.2 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-02 HAP-02 Vanadium (V) 17 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Antimony (Sb) 0.39 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Arsenic (As) 0.97 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Barium (Ba) 230 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Beryllium (Be) 0.64 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Cadmium (Cd) 0.18 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Chromium (Cr) 5.5 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Cobalt (Co) 1.6 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Copper (Cu) 9 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Lead (Pb) 5.4 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Manganese (Mn) 14 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Mercury (Hg) 0.029 parts per million (dry FALSE) (ppm)

Page 67
fuel_sample_pollutants

4042 VAPP-HAP-03 HAP-03 Nickel (Ni) 4.6 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Selenium (Se) 0.94 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-03 HAP-03 Vanadium (V) 15 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Antimony (Sb) 0.4 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Arsenic (As) 1 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Barium (Ba) 200 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Beryllium (Be) 0.56 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Cadmium (Cd) 0.12 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Chromium (Cr) 4 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Cobalt (Co) 1.3 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Copper (Cu) 7.5 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Lead (Pb) 5.4 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Manganese (Mn) 8.9 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Mercury (Hg) 0.018 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Nickel (Ni) 3.7 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Selenium (Se) 0.86 parts per million (dry FALSE) (ppm)

4042 VAPP-HAP-04 HAP-04 Vanadium (V) 13 parts per million (dry FALSE) (ppm)

Page 68
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

4042 VAPP-PM-B1B2-8.2005 compliance Particulate emission test to determine particulate emission rates during specified 8/30/2005 8/31/2005 Yes No

4042 VAPP-PM-B1B2-8.2009 Particulate matter compliance test at Valley 8/18/2009 8/19/2009 No Power Plant at the outlet of Boilers 1 No

4042 VAPP-PM-B1B2B3B4-8.2005 other Consent Decree Detrmine the particulate emission rates during normal operation conditions for B8/30/2005 9/2/2005 No No

4042 VAPP-PM-B3-12.2009 compliance Determine particulate matter emissions during normal operating conditions. 12/8/2009 12/8/2009 No No

4042 VAPP-PM-B3B4-8.2007 compliance Biennial particulate m 8/7/2007atter emissions testing for boilers 3 and 4. 8/8/2007 No No

4042 VAPP-PM-B4-12.2009 compliance Determine particulate matter emissions during normal operation. ######## ######## No No

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 compliance Determine particulate and gaseous emission rates during normal operating cond8/3/2006 8/4/2006 No No

Page 69
test_reports

deviation_reports

No

No

No

No

No

No

No

Page 70
test_report_configurations

facility_id report_id configuration_id

4042 VAPP-PM-B1B2-8.2005 VAPP-B1

4042 VAPP-PM-B1B2-8.2005 VAPP-B2

4042 VAPP-PM-B1B2-8.2009 VAPP-B1

4042 VAPP-PM-B1B2-8.2009 VAPP-B2

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-B1

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-B2

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-B3

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-B4

4042 VAPP-PM-B3-12.2009 VAPP-B3

4042 VAPP-PM-B3B4-8.2007 VAPP-B3

4042 VAPP-PM-B3B4-8.2007 VAPP-B4

4042 VAPP-PM-B4-12.2009 VAPP-B4

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-B3

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-B4

Page 71
test_report_fuels

facility_id report_id fuel_id

Page 72
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

Page 73
cem_data

facility_id time_periodcem_period_description

Page 74
cem_data_pollutants1

facility_id time_periodpollutant_name

Page 75
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B1No No

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B2No No

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 No No

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 No No

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 No No

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 No No

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH1 No No

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH2 No No

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH3 No No

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH4 No No

4042 VAPP-PM-B3-12.2009 VAPP-SP-BH3 No No

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 No No

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 No No

4042 VAPP-PM-B4-12.2009 VAPP-SP-BH4 No No

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 No No

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 No No

Page 76
test_report_sampling

fg_fraction

Each boiler (B1 and B2) enters it's own baghouse before entering a common stack.

Each boiler (B1 and B2) enters it's own baghouse before entering a common stack.

Each boiler (B1 and B2) enters it's own baghouse before entering a common stack.

Each boiler (B1 and B2) enters it's own baghouse before entering a common stack.

Each boiler (B1 and B2) enters it's own baghouse before entering a common stack.

Each boiler (B1 and B2) enters it's own baghouse before entering a common stack.

Each boiler enters (and exits) it's own baghouse before entering a common stack (Boilers 1/2 utilizes common stack S11, while 

Each boiler enters (and exits) it's own baghouse before entering a common stack (Boilers 1/2 utilizes common stack S11, while 

Each boiler enters (and exits) it's own baghouse before entering a common stack (Boilers 1/2 utilizes common stack S11, while 

Each boiler enters (and exits) it's own baghouse before entering a common stack (Boilers 1/2 utilizes common stack S11, while 

Each boiler (B3 and B4) enters it's own baghouse before entering a common stack.

Each boiler (B3 and B4) enters it's own baghouse before entering a common stack.

Each boiler (B3 and B4) enters it's own baghouse before entering a common stack.

Each boiler (B3 and B4) enters it's own baghouse before entering a common stack.

Page 77
test_report_sampling

1/2 utilizes common stack S11, while Boilers 3/4 utilizes stack S12).

1/2 utilizes common stack S11, while Boilers 3/4 utilizes stack S12).

1/2 utilizes common stack S11, while Boilers 3/4 utilizes stack S12).

1/2 utilizes common stack S11, while Boilers 3/4 utilizes stack S12).

Page 78
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B11 8/30/2005 8/30/2005 139 7.3

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B12 8/30/2005 8/30/2005 133 8

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B13 8/30/2005 8/30/2005 138 7.2

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B21 8/31/2005 8/31/2005 140 8.2

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B22 8/31/2005 8/31/2005 140 8.4

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B23 8/31/2005 8/31/2005 140 8.8

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 1 8/30/2005 8/30/2005 139 9

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 2 8/30/2005 8/30/2005 133 9.2

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 3 8/30/2005 8/30/2005 138 8

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 1 8/31/2005 8/31/2005 140 8

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 2 8/31/2005 8/31/2005 140 8

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 3 8/31/2005 8/31/2005 140 9.1

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 1 8/18/2009 8/18/2009 129 120 8.9

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 2 8/18/2009 8/18/2009 129 120 8.7

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 3 8/18/2009 8/18/2009 129 119 8.5

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 1 8/19/2009 8/19/2009 129 119 8.6

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 2 8/19/2009 8/19/2009 129 120 10

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 3 8/19/2009 8/19/2009 129 120 8.9

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH1 1 8/30/2005 8/30/2005 139 9

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH1 2 8/30/2005 8/30/2005 133 9.2

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH1 3 8/30/2005 8/30/2005 138 8

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH2 1 8/31/2005 8/31/2005 140 8

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH2 2 8/31/2005 8/31/2005 140 8

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH2 3 8/31/2005 8/31/2005 140 9.1

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH3 1 9/2/2005 9/2/2005 140 7.4

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH3 2 9/2/2005 9/2/2005 140 8

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH3 3 9/2/2005 9/2/2005 140 6.3

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH4 1 9/2/2005 9/2/2005 140 7.7

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH4 2 9/2/2005 9/2/2005 140 8.5

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH4 3 9/2/2005 9/2/2005 140 7.5

4042 VAPP-PM-B3-12.2009 VAPP-SP-BH3 1 12/8/2009 12/8/2009 6.7

4042 VAPP-PM-B3-12.2009 VAPP-SP-BH3 2 12/8/2009 12/8/2009 7.2

4042 VAPP-PM-B3-12.2009 VAPP-SP-BH3 3 12/8/2009 12/8/2009 8.2

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 1 8/7/2007 8/7/2007 6.9

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 2 8/7/2007 8/7/2007 7.4

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 3 8/7/2007 8/7/2007 8.4

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 1 8/8/2007 8/8/2007 8.8

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 2 8/8/2007 8/8/2007 8.3

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 3 8/8/2007 8/8/2007 8

4042 VAPP-PM-B4-12.2009 VAPP-SP-BH4 1 ######## ######## 5.5

4042 VAPP-PM-B4-12.2009 VAPP-SP-BH4 2 ######## ######## 5.4

4042 VAPP-PM-B4-12.2009 VAPP-SP-BH4 3 ######## ######## 6.1

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 1 8/3/2006 8/3/2006 6.2

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 2 8/3/2006 8/3/2006 7.2

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 3 8/3/2006 8/3/2006 7.2

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 1 8/4/2006 8/4/2006 6.5

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 2 8/4/2006 8/4/2006 6.1

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 3 8/4/2006 8/4/2006 6.4

Page 79
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

41.881 dscfm 63.33 1 8.5 12.5 1

39.389 dscfm 63.33 1 8.6 12.4 1

40.257 dscfm 68.33 1 8.6 12.4 1

40.321 dscfm 63.33 1 8 12 1

36.681 dscfm 63.33 1 8 12 1

38.722 dscfm 63.33 1 8 12 1

43.185 dscfm 66.33 1 6 13 1

41.374 dscfm 66.33 1 6 13 1

42.158 dscfm 66.33 1 6 13 1

42.762 dscfm 63.33 1 6 13 300

41.428 dscfm 63.33 1 6 13 1

43.732 dscfm 63.33 1 6 13 1

33.585 dscfm 68.33 1 6.4 12 1

33.762 dscfm 68.33 1 6 12.8 1

34.292 dscfm 68.33 1 6.6 12 1

32.552 dscfm 68.33 1 6.8 12 1

29.933 dscfm 68.33 1 7 11.8 1

31.575 dscfm 68.33 1 7 12 1

43.185 dscfm 68.33 1 6 13 1

41.374 dscfm 68.33 1 6 13 1

42.158 dscfm 68.33 1 6 13 1

42.762 dscfm 68.33 1 6 13 300

41.428 dscfm 68.33 1 6 13 1

43.732 dscfm 68.33 1 6 13 1

71.091 dscfm 68.33 1 6.9 13.2 1

69.062 dscfm 68.33 1 6.9 13.2 1

65.817 dscfm 68.33 1 6.9 13.2 1

69.752 dscfm 68.33 1 7 13 1

69.615 dscfm 68.33 1 7 13 1

69.91 dscfm 68.33 1 7 13 1

176482 dscfm 68.33 1 6.8 12.3 298.2

183357 dscfm 68.33 1 6.8 12.2 299.4

179824 dscfm 68.33 1 6.7 12.2 300

41.111 dscfm 68.33 1 6.5 12.5 1

42.003 dscfm 68.33 1 6.6 12.5 1

40.834 dscfm 68.33 1 6.6 12.5 1

36.318 dscfm 68.33 1 7.2 12 298.8

36.828 dscfm 68.33 1 6.7 12.3 299.6

36.438 dscfm 68.33 1 6.8 12.3 1

180244 dscfm 68.33 1 6.8 12.4 1

185266 dscfm 68.33 1 6.8 12.4 1

177641 dscfm 68.33 1 6.6 12.6 1

36.97 dscfm 68.33 1 7 12.2 1

37.009 dscfm 68.33 1 7.2 12.1 1

37.882 dscfm 68.33 1 7.2 12.1 1

36.282 dscfm 68.33 1 6.7 12.5 1

35.581 dscfm 68.33 1 6.6 12.5 1

35.404 dscfm 68.33 1 6.6 12.6 1

Page 80
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

0.947 Method 2, Method 3, Method 17

0.947 Method 2, Method 3, Method 17 Soot blowing

0.947 Method 2, Method 3, Method 17 Soot blowing

0.947 Method 2, Method 3, Method 17

0.947 Method 2, Method 3, Method 17

0.947 Method 2, Method 3, Method 17 Soot blowing

0.947 Method 2, Method 3, Method 5, and Method 202

0.947 Method 2, Method 3, Method 5, and Method 202 Soot blowing

0.947 Method 2, Method 3, Method 5, and Method 202 Soot blowing

0.94 Method 2, Method 3, Method 5, and Method 202

0.94 Method 2, Method 3, Method 5, and Method 202

0.94 Method 2, Method 3, Method 5, and Method 202 Soot blowing

0.939 Method 1, Method 2, Method 3A, Method 5 and 202

0.939 Method 1, Method 2, Method 3A, Method 5 and 202

0.939 Method 1, Method 2, Method 3A, Method 5 and 202 Soot blowing

0.94 Method 1, Method 2, Method 3A, Method 5 and 202

0.94 Method 1, Method 2, Method 3A, Method 5 and 202

0.94 Method 1, Method 2, Method 3A, Method 5 and 202 Soot blowing

0.943 Method 2, Method 3, Method 5

0.943 Method 2, Method 3, Method 5

0.943 Method 2, Method 3, Method 5

0.973 Method 2, Method 3, Method 5

0.973 Method 2, Method 3, Method 5

0.973 Method 2, Method 3, Method 5 Soot blowing

0.945 Method 2, Method 3, Method 5

0.945 Method 2, Method 3, Method 5

0.945 Method 2, Method 3, Method 5

0.953 Method 2, Method 3, Method 5

0.953 Method 2, Method 3, Method 5

0.953 Method 2, Method 3, Method 5

0.936 Method 1, Method 2, Method 3A, Method 5

0.937 Method 1, Method 2, Method 3A, Method 5

0.94 Method 1, Method 2, Method 3A, Method 5

0.943 Method 1, Method 2, Method 3A, Method 5 and 202

0.943 Method 1, Method 2, Method 3A, Method 5 and 202

0.943 Method 1, Method 2, Method 3A, Method 5 and 202

0.942 Method 1, Method 2, Method 3A, Method 5 and 202

0.942 Method 1, Method 2, Method 3A, Method 5 and 202

0.942 Method 1, Method 2, Method 3A, Method 5 and 202

0.944 Method 1, Method 2, Method 3A, Method 5

0.944 Method 1, Method 2, Method 3A, Method 5

0.944 Method 1, Method 2, Method 3A, Method 5

0.94 Method 2, Method 3A, Method 5 and 202, Method 25A, Method 18, Method 10

0.94 Method 2, Method 3A, Method 5 and 202, Method 25A, Method 18, Method 10

0.94 Method 2, Method 3A, Method 5 and 202, Method 25A, Method 18, Method 10

0.936 Method 2, Method 3A, Method 5 and 202, Method 25A, Method 18, Method 10

0.936 Method 2, Method 3A, Method 5 and 202, Method 25A, Method 18, Method 10

0.936 Method 2, Method 3A, Method 5 and 202, Method 25A, Method 18, Method 10

Page 81
sampling_runs

fuel_sulfur

Page 82
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 2 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 3 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 3 PM (Condensable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 1 PM (Filterable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 1 PM (Condensable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 2 PM (Filterable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 2 PM (Condensable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 3 PM (Filterable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 3 PM (Condensable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 1 Carbon Monoxide (CO) 80.1 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 1 Total Hydrocarbons (THC) (as Methane) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 1 Methane (CH4) 0.42 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 2 Carbon Monoxide (CO) 76 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 2 Total Hydrocarbons (THC) (as Methane) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 2 Methane (CH4) 0.43 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 3 Carbon Monoxide (CO) 75.7 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 3 Total Hydrocarbons (THC) (as Methane) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH3 3 Methane (CH4) 0.28 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 1 PM (Filterable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 1 PM (Condensable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 1 Carbon Monoxide (CO) 58.3 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 1 Total Hydrocarbons (THC) (as Methane) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 1 Methane (CH4) 0.48 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 2 PM (Filterable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 2 PM (Condensable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 2 Carbon Monoxide (CO) 67.6 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 2 Total Hydrocarbons (THC) (as Methane) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 2 Methane (CH4) 0.29 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 3 PM (Filterable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 3 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B11 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B12 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B13 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 1 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 2 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 3 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH1 3 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B21 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B22 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-B23 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2005 VAPP-SP-BH2 1 PM (Condensable) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 3 Carbon Monoxide (CO) 72.1 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 3 Total Hydrocarbons (THC) (as Methane) FALSE

4042 VAPP-PM-CO-THC-CH4-B3B4-8.2006 VAPP-SP-BH4 3 Methane (CH4) 0.23 parts per million by FALSE volume (dry) (ppmvd)

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 1 PM (Filterable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 1 PM (Condensable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 2 PM (Filterable) FALSE

Page 83
sampling_run_pollutants1

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 2 PM (Condensable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 3 PM (Filterable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH3 3 PM (Condensable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 1 PM (Filterable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 1 PM (Condensable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 2 PM (Filterable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 2 PM (Condensable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 3 PM (Filterable) FALSE

4042 VAPP-PM-B3B4-8.2007 VAPP-SP-BH4 3 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 1 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 2 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 3 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH1 3 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 1 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 2 PM (Condensable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 3 PM (Filterable) FALSE

4042 VAPP-PM-B1B2-8.2009 VAPP-SP-BH2 3 PM (Condensable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH1 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH1 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH1 3 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH2 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH2 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH2 3 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH3 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH3 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH3 3 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH4 1 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH4 2 PM (Filterable) FALSE

4042 VAPP-PM-B1B2B3B4-8.2005 VAPP-SP-BH4 3 PM (Filterable) FALSE

4042 VAPP-PM-B3-12.2009 VAPP-SP-BH3 1 PM (Filterable) FALSE

4042 VAPP-PM-B3-12.2009 VAPP-SP-BH3 2 PM (Filterable) FALSE

4042 VAPP-PM-B3-12.2009 VAPP-SP-BH3 3 PM (Filterable) FALSE

4042 VAPP-PM-B4-12.2009 VAPP-SP-BH4 1 PM (Filterable) FALSE

4042 VAPP-PM-B4-12.2009 VAPP-SP-BH4 2 PM (Filterable) FALSE

4042 VAPP-PM-B4-12.2009 VAPP-SP-BH4 3 PM (Filterable) FALSE

Page 84
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

4.59 pound per hour (lb/hr) FALSE 0.0056 pound per million British Thermal Unit (lb/MMBtu) FALSE

24.259 pound per hour (lb/hr) FALSE 0.0297 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.619 pound per hour (lb/hr) FALSE 0.0055 pound per million British Thermal Unit (lb/MMBtu) FALSE

36.839 pound per hour (lb/hr) FALSE 0.0436 pound per million British Thermal Unit (lb/MMBtu) FALSE

8.736 pound per hour (lb/hr) FALSE 0.0114 pound per million British Thermal Unit (lb/MMBtu) FALSE

48.252 pound per hour (lb/hr) FALSE 0.063 pound per million British Thermal Unit (lb/MMBtu) FALSE

10.078 pound per hour (lb/hr) FALSE 0.0132 pound per million British Thermal Unit (lb/MMBtu) FALSE

77.513 pound per hour (lb/hr) FALSE 0.1018 pound per million British Thermal Unit (lb/MMBtu) FALSE

7.986 pound per hour (lb/hr) FALSE 0.0104 pound per million British Thermal Unit (lb/MMBtu) FALSE

82.127 pound per hour (lb/hr) FALSE 0.1071 pound per million British Thermal Unit (lb/MMBtu) FALSE

65.6 pound per hour (lb/hr) FALSE 0.086 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.63 pound per hour (lb/hr) FALSE 0.0008 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE PPMV, not ppmvd

62.7 pound per hour (lb/hr) FALSE 0.082 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.89 pound per hour (lb/hr) FALSE 0.0012 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE reported as PPMV, not ppmvd

62.9 pound per hour (lb/hr) FALSE 0.082 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.32 pound per hour (lb/hr) FALSE 0.0004 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE reported as PPMV, not ppmvd

8.033 pound per hour (lb/hr) FALSE 0.0101 pound per million British Thermal Unit (lb/MMBtu) FALSE

70.632 pound per hour (lb/hr) FALSE 0.0892 pound per million British Thermal Unit (lb/MMBtu) FALSE

48.3 pound per hour (lb/hr) FALSE 0.061 pound per million British Thermal Unit (lb/MMBtu) FALSE

1.32 pound per hour (lb/hr) FALSE 0.0017 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE reported as PPMV, not ppmvd

7.709 pound per hour (lb/hr) FALSE 0.0097 pound per million British Thermal Unit (lb/MMBtu) FALSE

43.453 pound per hour (lb/hr) FALSE 0.0549 pound per million British Thermal Unit (lb/MMBtu) FALSE

55.6 pound per hour (lb/hr) FALSE 0.07 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.4 pound per hour (lb/hr) FALSE 0.0005 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE reported as PPMV, not ppmvd

6.326 pound per hour (lb/hr) FALSE 0.0081 pound per million British Thermal Unit (lb/MMBtu) FALSE

51.445 pound per hour (lb/hr) FALSE 0.0659 pound per million British Thermal Unit (lb/MMBtu) FALSE

10210.78 pound per hour (lb/hr) FALSE 14.4212 pound per million British Thermal Unit (lb/MMBtu) FALSE

15705.32 pound per hour (lb/hr) FALSE 23.9521 pound per million British Thermal Unit (lb/MMBtu) FALSE

7344.024 pound per hour (lb/hr) FALSE 10.7943 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.346 pound per hour (lb/hr) FALSE 0.0063 pound per million British Thermal Unit (lb/MMBtu) FALSE

15.445 pound per hour (lb/hr) FALSE 0.0182 pound per million British Thermal Unit (lb/MMBtu) FALSE

11.045 pound per hour (lb/hr) FALSE 0.0137 pound per million British Thermal Unit (lb/MMBtu) FALSE

33.487 pound per hour (lb/hr) FALSE 0.0417 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.312 pound per hour (lb/hr) FALSE 0.0063 pound per million British Thermal Unit (lb/MMBtu) FALSE

18.833 pound per hour (lb/hr) FALSE 0.0224 pound per million British Thermal Unit (lb/MMBtu) FALSE

7593.492 pound per hour (lb/hr) FALSE 10.8946 pound per million British Thermal Unit (lb/MMBtu) FALSE

5041.419 pound per hour (lb/hr) FALSE 7.9131 pound per million British Thermal Unit (lb/MMBtu) FALSE

9190.285 pound per hour (lb/hr) FALSE 13.5426 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.619 pound per hour (lb/hr) FALSE 0.0054 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.919 pound per hour (lb/hr) FALSE 0.0058 pound per million British Thermal Unit (lb/MMBtu) FALSE

58.5 pound per hour (lb/hr) FALSE 0.075 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.14 pound per hour (lb/hr) FALSE 0.0002 pound per million British Thermal Unit (lb/MMBtu) FALSE

FALSE FALSE reported as PPMV, not ppmvd

9.68 pound per hour (lb/hr) FALSE 0.0114 pound per million British Thermal Unit (lb/MMBtu) FALSE

9.615 pound per hour (lb/hr) FALSE 0.0113 pound per million British Thermal Unit (lb/MMBtu) FALSE

9.886 pound per hour (lb/hr) FALSE 0.0118 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 85
sampling_run_pollutants1

8.123 pound per hour (lb/hr) FALSE 0.0097 pound per million British Thermal Unit (lb/MMBtu) FALSE

14.072 pound per hour (lb/hr) FALSE 0.0173 pound per million British Thermal Unit (lb/MMBtu) FALSE

8.795 pound per hour (lb/hr) FALSE 0.0108 pound per million British Thermal Unit (lb/MMBtu) FALSE

6.369 pound per hour (lb/hr) FALSE 0.0091 pound per million British Thermal Unit (lb/MMBtu) FALSE

9.711 pound per hour (lb/hr) FALSE 0.0139 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.938 pound per hour (lb/hr) FALSE 0.008 pound per million British Thermal Unit (lb/MMBtu) FALSE

9.832 pound per hour (lb/hr) FALSE 0.0133 pound per million British Thermal Unit (lb/MMBtu) FALSE

10.687 pound per hour (lb/hr) FALSE 0.0146 pound per million British Thermal Unit (lb/MMBtu) FALSE

17.086 pound per hour (lb/hr) FALSE 0.0234 pound per million British Thermal Unit (lb/MMBtu) FALSE

13.267 pound per hour (lb/hr) FALSE 0.0169 pound per million British Thermal Unit (lb/MMBtu) FALSE

37.323 pound per hour (lb/hr) FALSE 0.0476 pound per million British Thermal Unit (lb/MMBtu) FALSE

8.134 pound per hour (lb/hr) FALSE 0.0101 pound per million British Thermal Unit (lb/MMBtu) FALSE

41.613 pound per hour (lb/hr) FALSE 0.0515 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.129 pound per hour (lb/hr) FALSE 0.0053 pound per million British Thermal Unit (lb/MMBtu) FALSE

44.046 pound per hour (lb/hr) FALSE 0.0561 pound per million British Thermal Unit (lb/MMBtu) FALSE

9.161 pound per hour (lb/hr) FALSE 0.0123 pound per million British Thermal Unit (lb/MMBtu) FALSE

9.601 pound per hour (lb/hr) FALSE 0.0129 pound per million British Thermal Unit (lb/MMBtu) FALSE

8.192 pound per hour (lb/hr) FALSE 0.0124 pound per million British Thermal Unit (lb/MMBtu) FALSE

27.307 pound per hour (lb/hr) FALSE 0.0413 pound per million British Thermal Unit (lb/MMBtu) FALSE

10.71 pound per hour (lb/hr) FALSE 0.015 pound per million British Thermal Unit (lb/MMBtu) FALSE

31.543 pound per hour (lb/hr) FALSE 0.0443 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.346 pound per hour (lb/hr) FALSE 0.0063 pound per million British Thermal Unit (lb/MMBtu) FALSE

11.045 pound per hour (lb/hr) FALSE 0.0137 pound per million British Thermal Unit (lb/MMBtu) FALSE

5.312 pound per hour (lb/hr) FALSE 0.0063 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.619 pound per hour (lb/hr) FALSE 0.0054 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.59 pound per hour (lb/hr) FALSE 0.0056 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.619 pound per hour (lb/hr) FALSE 0.0055 pound per million British Thermal Unit (lb/MMBtu) FALSE

0.608 pound per hour (lb/hr) FALSE 0.0007 pound per million British Thermal Unit (lb/MMBtu) FALSE

8.839 pound per hour (lb/hr) FALSE 0.0109 pound per million British Thermal Unit (lb/MMBtu) FALSE

2.466 pound per hour (lb/hr) FALSE 0.0031 pound per million British Thermal Unit (lb/MMBtu) FALSE

2.658 pound per hour (lb/hr) FALSE 0.0033 pound per million British Thermal Unit (lb/MMBtu) FALSE

1.71 pound per hour (lb/hr) FALSE 0.0021 pound per million British Thermal Unit (lb/MMBtu) FALSE

1.762 pound per hour (lb/hr) FALSE 0.0022 pound per million British Thermal Unit (lb/MMBtu) FALSE

6.073 pound per hour (lb/hr) FALSE 0.0083 pound per million British Thermal Unit (lb/MMBtu) FALSE

8.126 pound per hour (lb/hr) FALSE 0.0108 pound per million British Thermal Unit (lb/MMBtu) FALSE

4.433 pound per hour (lb/hr) FALSE 0.0059 pound per million British Thermal Unit (lb/MMBtu) FALSE

10.793 pound per hour (lb/hr) FALSE 0.0145 pound per million British Thermal Unit (lb/MMBtu) FALSE

8.917 pound per hour (lb/hr) FALSE 0.0117 pound per million British Thermal Unit (lb/MMBtu) FALSE

7.385 pound per hour (lb/hr) FALSE 0.0099 pound per million British Thermal Unit (lb/MMBtu) FALSE

Page 86
sampling_run_pollutants1

run_pollutant_comment

PPMV, not ppmvd

reported as PPMV, not ppmvd

reported as PPMV, not ppmvd

reported as PPMV, not ppmvd

reported as PPMV, not ppmvd

reported as PPMV, not ppmvd

Page 87
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

Page 88
sampling_run_fuel

fuel_conc_MDL

Page 89