```

[Federal Register Volume 81, Number 61 (Wednesday, March 30, 2016)]
[Notices]
[Pages 17697-17708]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2016-07185]

-----------------------------------------------------------------------

ENVIRONMENTAL PROTECTION AGENCY

[FRL-9944-39-OA]

Applicability Determination Index (ADI) Data System Recent 
Posting: Agency Applicability Determinations, Alternative Monitoring 
Decisions, and Regulatory Interpretations Pertaining to Standards of 
Performance for New Stationary Sources, National Emission Standards for 
Hazardous Air Pollutants, and the Stratospheric Ozone Protection 
Program

AGENCY: Environmental Protection Agency (EPA).

ACTION: Notice of availability.

-----------------------------------------------------------------------

SUMMARY: This notice announces applicability determinations, 
alternative monitoring decisions, and regulatory interpretations that 
the Environmental Protection Agency (EPA) has made under the New Source 
Performance Standards (NSPS); the National Emission Standards for 
Hazardous Air Pollutants (NESHAP); and/or the Stratospheric Ozone 
Protection Program.

FOR FURTHER INFORMATION CONTACT: An electronic copy of each complete 
document posted on the Applicability Determination Index (ADI) data 
system is available on the Internet through the Resources and Guidance 
Documents for Compliance Assistance page of the Clean Air Act 
Compliance Monitoring Web site under ``Air'' at: https://www2.epa.gov/compliance/resources-and-guidance-documents-compliance-assistance. The 
letters and memoranda on the ADI may be located by date, office of 
issuance, subpart, citation, control number, or by string word 
searches. For questions about the ADI or this notice, contact Maria 
Malave at EPA by phone at: (202) 564-7027, or by email at: 
malave.maria@epa.gov. For technical questions about individual 
applicability determinations, monitoring decisions or regulatory 
interpretations, refer to the contact person identified in the 
individual documents, or in the absence of a contact person, refer to 
the author of the document.

SUPPLEMENTARY INFORMATION: 

Background

    The General Provisions of the NSPS in 40 Code of Federal 
Regulations (CFR) part 60 and the General Provisions of the NESHAP in 
40 CFR part 61 provide that a source owner or operator may request a 
determination of whether certain intended actions constitute the 
commencement of construction,

[[Page 17698]]

reconstruction, or modification. EPA's written responses to these 
inquiries are commonly referred to as applicability determinations. See 
40 CFR 60.5 and 61.06. Although the NESHAP part 63 regulations [which 
include Maximum Achievable Control Technology (MACT) standards and/or 
Generally Available Control Technology (GACT) standards] and Section 
111(d) of the Clean Air Act (CAA) contain no specific regulatory 
provision providing that sources may request applicability 
determinations, EPA also responds to written inquiries regarding 
applicability for the part 63 and Section 111(d) programs. The NSPS and 
NESHAP also allow sources to seek permission to use monitoring or 
recordkeeping that is different from the promulgated requirements. See 
40 CFR 60.13(i), 61.14(g), 63.8(b)(1), 63.8(f), and 63.10(f). EPA's 
written responses to these inquiries are commonly referred to as 
alternative monitoring decisions. Furthermore, EPA responds to written 
inquiries about the broad range of NSPS and NESHAP regulatory 
requirements as they pertain to a whole source category. These 
inquiries may pertain, for example, to the type of sources to which the 
regulation applies, or to the testing, monitoring, recordkeeping, or 
reporting requirements contained in the regulation. EPA's written 
responses to these inquiries are commonly referred to as regulatory 
interpretations.
    EPA currently compiles EPA-issued NSPS and NESHAP applicability 
determinations, alternative monitoring decisions, and regulatory 
interpretations, and posts them to the ADI on a regular basis. In 
addition, the ADI contains EPA-issued responses to requests pursuant to 
the stratospheric ozone regulations, contained in 40 CFR part 82. The 
ADI is a data system on the Internet with over three thousand EPA 
letters and memoranda pertaining to the applicability, monitoring, 
recordkeeping, and reporting requirements of the NSPS, NESHAP, and 
stratospheric ozone regulations. Users can search for letters and 
memoranda by date, office of issuance, subpart, citation, control 
number, or by string word searches.
    Today's notice comprises a summary of 66 such documents added to 
the ADI on March 22, 2016. This notice lists the subject and header of 
each letter and memorandum, as well as a brief abstract of the letter 
or memorandum. Complete copies of these documents may be obtained from 
the ADI on the Internet through the Resources and Guidance Documents 
for Compliance Assistance page of the Clean Air Act Compliance 
Monitoring Web site under ``Air'' at: https://www2.epa.gov/compliance/resources-and-guidance-documents-compliance-assistance.

Summary of Headers and Abstracts

    The following table identifies the control number for each document 
posted on the ADI data system on March 22, 2016; the applicable 
category; the section(s) and/or subpart(s) of 40 CFR part 60, 61, or 63 
(as applicable) addressed in the document; and the title of the 
document, which provides a brief description of the subject matter.
    We have also included an abstract of each document identified with 
its control number after the table. These abstracts are provided solely 
to alert the public to possible items of interest and are not intended 
as substitutes for the full text of the documents. This notice does not 
change the status of any document with respect to whether it is ``of 
nationwide scope or effect'' for purposes of CAA section 307(b)(1) For 
example, this notice does not convert an applicability determination 
for a particular source into a nationwide rule. Neither does it purport 
to make a previously non-binding document binding.

                                  ADI Determinations Uploaded on March 22, 2016
----------------------------------------------------------------------------------------------------------------
           Control No.                  Categories             Subparts                      Title
----------------------------------------------------------------------------------------------------------------
1500021..........................  NSPS................  J..................  Change to Alternative Sulfur
                                                                               Monitoring Plan for Flare System.
1500022..........................  NSPS................  J..................  Alternative to Hydrogen Sulfide
                                                                               Monitoring for Flare System.
1500023..........................  NSPS................  EEEE...............  Applicability Determination for a
                                                                               Rural Institutional Waste
                                                                               Incinerator.
1500024..........................  NSPS................  DD.................  Regulatory Interpretation for
                                                                               Grain Elevators with Expanded
                                                                               Capacity.
1500025..........................  NSPS................  AAAA...............  Applicability Determination for a
                                                                               Small Municipal Waste Combustor.
1500026..........................  NSPS................  Y..................  NSPS Source Test Plan Approval.
1500027..........................  NSPS................  A, DD..............  Performance Test Waivers for New
                                                                               Design and Identical Units at
                                                                               Grain Elevators.
1500028..........................  NSPS................  A, JJJJ............  Test Waiver for Identical Biogas-
                                                                               fueled Generators.
1500029..........................  NSPS................  A, JJJJ............  30-Day Advance Test Notice Waiver
                                                                               for Generators.
1500030..........................  NSPS................  CCCC, EEEE.........  Applicability Determination for
                                                                               Incinerator Burning MSW or RDF.
1500031..........................  NSPS................  Dc.................  Applicability Determination for
                                                                               Boiler De-rating.
1500033..........................  NSPS................  KKKK...............  Request for Performance Test
                                                                               Waiver at Combustion Turbine.
1500034..........................  NSPS................  Ec.................  Alternative Monitoring of Waste
                                                                               Combusted.
1500035..........................  NSPS................  CCCC...............  Applicability Determination for
                                                                               Incinerator Burning MSW or RDF.
1500036..........................  NSPS................  GG.................  Monitoring at Turbines During Non-
                                                                               Operational Periods.
1500038..........................  NSPS................  A, JJJJ............  30-Day Advance Test Notice Waiver
                                                                               for Generators.
1500039..........................  NSPS................  Cb, Eb.............  Carbon Feed Rate Monitoring Waiver
                                                                               Request.
1500049..........................  NSPS................  KKKK...............  Performance Test Waiver for
                                                                               Identical Turbines.
1500051..........................  NSPS................  J, Ja..............  Alternative Monitoring Plan for
                                                                               Tank Degassing and Vapor Control
                                                                               Projects at Petroleum Refineries.
1500054..........................  NSPS................  NNN................  Alternative Monitoring for an
                                                                               Absorber on a Distillation Unit.
1500056..........................  NSPS................  OOO................  Applicability Determination for
                                                                               Nonmetallic Mineral Processing
                                                                               Loading Station Enclosed in a
                                                                               Building.
1500057..........................  NSPS................  Ce, Ec.............  Alternative Monitoring for Wet
                                                                               Scrubber at a Waste Incinerator.
1500058..........................  NSPS................  J..................  Alternative Monitoring for Wet Gas
                                                                               Scrubber In Lieu of COMS at an
                                                                               FCCU.
1500059..........................  NSPS................  IIII...............  Emergency Generator Applicability
                                                                               with Respect to Readiness Testing
                                                                               and Commissioning.
1500060..........................  MACT, NESHAP, NSPS..  IIII, ZZZZ.........  Regulatory Interpretation of NSPS
                                                                               and NESHAP Emergency Internal
                                                                               Combustion Engine Provisions.

[[Page 17699]]

 
1500062..........................  NSPS................  Ja.................  Alternative Monitoring of Hydrogen
                                                                               Sulfide and TRS in Sour Gas
                                                                               Routed to Flares.
1500063..........................  NSPS................  J..................  Alternative Monitoring Plan for
                                                                               Wet Gas Scrubber at a Refinery.
1500064..........................  NSPS................  OOOO...............  Alternate Reporting Schedule for
                                                                               Gas Plant.
1500065..........................  NSPS................  JJJJ...............  Applicability Determination and
                                                                               Testing Waiver Request for Spark
                                                                               Ignition Engines.
1500066..........................  NSPS................  JJJJ...............  Alternative Testing for Spark
                                                                               Ignition Engines.
1500067..........................  NSPS................  IIII...............  Alternative Test Method Request
                                                                               for Compression Ignition Engines
                                                                               Switching to Biodiesel.
1500068..........................  NSPS................  J, Ja..............  Alternative Monitoring of Hydrogen
                                                                               Sulfide from Portable Thermal
                                                                               Oxidizers at Multiple Refineries.
1500069..........................  NSPS................  JJJJ...............  Alternative Test Method to Cutter
                                                                               Analyzers for Emissions from an
                                                                               Internal Combustion Engine.
1500071..........................  NSPS................  JJJJ...............  Alternative Test Method for Non-
                                                                               methane Organic Emissions from
                                                                               Stationary Spark Ignition
                                                                               Combustion Engines.
1500072..........................  NSPS................  J..................  Alternative Monitoring Plan for
                                                                               Hydrogen Sulfide Content of
                                                                               Refinery Fuel Gas.
1500073..........................  MACT, NSPS..........  ZZZZ, JJJJ.........  Alternative Test Method for Non-
                                                                               methane Organic Emissions from
                                                                               Stationary Spark Ignition
                                                                               Combustion Engines.
1500074..........................  NSPS................  Ec.................  Deadline for Initial Compliance
                                                                               Testing of a Waste Incinerator.
1600004..........................  NSPS................  DD.................  Clarification of the Definition of
                                                                               Permanent Storage Facilities.
A150001..........................  Asbestos............  M..................  Standard Practice for
                                                                               Comprehensive Building Asbestos
                                                                               Surveys.
C150001..........................  CFC.................  C..................  Regulatory Interpretation of
                                                                               Evaporator Coil Leak Repair
                                                                               Requirement.
M150010..........................  MACT, NESHAP, NSPS..  A, PPPPPP, KK......  Request for Opacity Test Waiver.
M150011..........................  MACT, NSPS..........  ZZZZ, IIII.........  Applicability of Emergency and
                                                                               Certified Engines to NSPS and
                                                                               NESHAP.
M150012..........................  MACT................  ZZZZ...............  Applicability Determination for
                                                                               Nonroad versus Stationary Engine.
M150013..........................  MACT, NESHAP........  HHHHHH.............  Applicability Determination for
                                                                               Vehicle Undercoating.
M150015..........................  MACT, NESHAP........  A, PPPPPP..........  Alternative Visible Emission
                                                                               Monitoring at a Lead Acid Battery
                                                                               Plant.
M150016..........................  MACT, NESHAP........  MMMMMM, YY.........  Applicability of Tire Reclamation
                                                                               Facility to Carbon Black
                                                                               Production NESHAP.
M150017..........................  MACT, NESHAP........  HHHHHH.............  Regulatory Interpretation of
                                                                               Applicability of Truck Bed Lining
                                                                               Operations to Area Source NESHAP
                                                                               for Paint Stripping and
                                                                               Miscellaneous Surface Coating.
M150023..........................  MACT................  LLL................  Alternative Monitoring for
                                                                               Particulate Matter on a Common
                                                                               Stack at a Portland Cement Plant.
M150024..........................  MACT................  S..................  Alternative Averaging Time for
                                                                               Inlet Flow Monitoring as a
                                                                               Surrogate for Methanol
                                                                               Destruction at a Pulp and Paper
                                                                               Facility.
M150025..........................  MACT................  ZZZZ...............  Alternative Load Level for
                                                                               Pressure Drop Measurement at
                                                                               Internal Combustion Engines.
M150026..........................  MACT, NSPS..........  ZZZZ, IIII.........  Applicability Determination for
                                                                               Internal Combustion Engine to
                                                                               NSPS and NESHAP.
M150027..........................  MACT................  ZZZZ...............  Applicability Determination for
                                                                               Remote Reciprocating Internal
                                                                               Combustion Engine.
M150028..........................  MACT................  DDDD, DDDDD........  Applicability Determination for
                                                                               Rotary Gasifiers as Process
                                                                               Heaters to the Boiler MACT.
M150029..........................  MACT................  ZZZZ...............  Performance Test Waiver for
                                                                               Reciprocating Internal Combustion
                                                                               Engines.
M150030..........................  MACT................  DDDDD..............  Applicability Determination for a
                                                                               Hybrid Suspension Grate Biomass
                                                                               Boiler under the Boiler MACT.
M150031..........................  MACT................  JJJJJJ.............  Applicability Determination for
                                                                               Electric Generating Units under
                                                                               the Boiler Area Source NESHAP.
M150034..........................  MACT................  ZZZZ...............  Applicability Determination for
                                                                               Backup Power Generator under RICE
                                                                               NESHAP.
M150036..........................  MACT, NESHAP........  A..................  60-day Advance Test Notice Waiver.
Z150002..........................  NESHAP..............  N..................  Applicability Determination for
                                                                               Manufacture of Colored Art Glass.
Z150004..........................  MACT, NESHAP, NSPS..  ZZZZ, Db, IIII,      Applicability Determination for
                                                          JJJJ.                Offshore Gas Port Emission Units.
Z150005..........................  MACT, NESHAP........  ZZZZ...............  Applicability Determination for
                                                                               Emergency Stationary Internal
                                                                               Combustion Engines at an
                                                                               Institutional Facility.
Z150006..........................  MACT, NESHAP........  ZZZZ...............  Regulatory Interpretation on
                                                                               Minimizing Engine Idle Time for
                                                                               Internal Combustion Engines.
Z150009..........................  MACT, NESHAP........  ZZZZ...............  Regulatory Interpretation of
                                                                               Emergency Generator Provisions
                                                                               under NESHAP Subpart ZZZZ.
Z150010..........................  MACT, NESHAP........  ZZZZ...............  Regulatory Interpretation on Rule
                                                                               Applicability to Stationary
                                                                               Engines.
Z150011..........................  MACT, NESHAP........  ZZZZ...............  Applicability Determination for
                                                                               Emergency Engines to RICE NESHAP.
----------------------------------------------------------------------------------------------------------------

[[Page 17700]]

Abstracts

Abstract for [1500021]

    Q: Will EPA approve a change to the previously approved March 22, 
2011 alternative monitoring plan (AMP) for Shell Oil Products Puget 
Sound Refinery (PSR) in Anacortes, Washington?
    A: Yes. EPA conditionally approves Shell's revision to the PSR 2011 
AMP. For the monitoring of H2S, PSR is requesting to monitor as 
required by NSPS subpart J, rather than the alternative monitoring 
method that was specified in the 2011 AMP. PSR requests that certain 
portions of the approved AMP stay in place to maintain approval of an 
alternative means for demonstrating compliance for three interconnected 
flares. The conditions that must be satisfied to allow PSR to rely on 
the AMP instead of utilizing an H2S continuous monitoring system 
according to subpart J are stated in the EPA approval letter.

Abstract for [1500022]

    Q: Will EPA approve an alternative monitoring plan (AMP) for the 
Shell Oil Anacortes, Washington facility to install, maintain, and 
operate a total sulfur continuous monitoring system (CMS) as an 
alternative to a hydrogen sulfide (H2S) CMS, and to use sulfur data 
collected at the east flare to represent the sulfur content at the 
north and south flares?
    A: Yes. EPA conditionally approves Shell's AMP for utilizing a H2S 
CMS. The conditions to allow Shell to rely on the AMP instead of 
utilizing an H2S CMS are stated in the EPA is approval letter.

Abstract for [1500023]

    Q: Will EPA grant approval of exempted status under 40 CFR 
60.2887(h) of the NSPS subpart EEEE as a rural institutional waste 
incinerator for an incineration unit that Glacier Bay National Park and 
Preserve (the Park) in Alaska intends to purchase and install?
    A: Yes. EPA determines that the proposed incinerator meets the 
exclusion for rural institutional waste incinerators because the unit 
is located more than 50 miles from the boundary of the nearest 
Metropolitan Statistical Area, alternative disposal options are not 
available or are economically infeasible, and the Park has submitted 
this request prior to initial startup of the incinerator.

Abstract for [1500024]

    Q: Are all on-site units at Kalama Export located in Kalama, 
Washington that were constructed after August 3, 1978, subject to NSPS 
subpart DD for Grain Elevators when applicability is triggered due to 
expanded capacity?
    A: No. In its response to the Southwest Clean Air Agency in 
Vancouver, Washington, EPA explains that the rule applies to each 
individual affected facility at a grain elevator. Therefore, only the 
units that are constructed, modified, or reconstructed when and after 
the NSPS is triggered because of expanded capacity become subject to 
the rule.

Abstract for [1500025]

    Q1: Does NSPS subpart AAAA for Small Municipal Waste Combustion 
(MWC) Units apply to gas combustion turbine that combust a small amount 
of non-condensable hydrocarbon gases, which is located at the Green 
Power facility in Pasco, Washington?
    A1: Yes. In a response to the Washington State Department of 
Ecology and the counsel to the source, EPA indicates that the NSPS 
subpart AAAA applies to the gas combustion turbine it is considered to 
be within the MWC unit boundaries and based on the capacity of the MWC. 
Based on the MWC definition at 40 CFR 60.1465, the catalytic pressure-
less de-polymerization process (CDP) begins the MWC since it is used to 
convert municipal solid waste into synthetic liquid petroleum fuel, 
which includes a small amount of non-condensable hydrocarbon gases. 
Since the non-condensable hydrocarbon gas generated by the CDP is 
combusted in the turbine, the compressor section and combustor section 
of the turbine at the facility are within the MWC boundaries. In 
addition, it is determine that the combustion capacity of the MWC, 
which would not include the capacity attributable to the flare since it 
is a control device, is within the applicable range of subpart AAAA. 
Furthermore, the Green Power operation does not combust landfill gases 
and the landfill gas exemption, therefore, is not applicable.
    Q2: Does NSPS subpart AAAA apply to the Green Power CDP if it 
operates in anaerobic environment, exposed only to inert gases, due to 
explosion hazard?
    A2: No. EPA determines that the Green Power CDP would not be 
subject to Subpart AAAA due to the absence of combustion if the plant 
is constructed such that there is no combustion of the synthetic fuel 
product.
    Q3: Does NSPS subpart AAAA apply to the Green Power proposed Algae 
Production Alternative whereby the non-condensable hydrocarbon gases 
produced in the reactor are routed to a biological treatment unit as a 
nutrient in the production of algae which would subsequently be 
harvested and reintroduced as a feedstock for the CDP process?
    A3: No. EPA determines that in this scenario Subpart AAAA would not 
apply due to the absence of combustion.

Abstract for [1500026]

    Q: Will EPA approve a source test plan submitted by Eielson Air 
Force Base in Alaska for a particulate matter source test on six bin 
vent filters for a new mechanical coal tipper subject to NSPS subpart 
Y?
    A: Yes. EPA approves the Eielson source test plan under subpart Y. 
Eielson has incorporated the guidance received by EPA regarding the 
proper location for a testing port installation to address issues with 
inadequate duct diameter sizing for that bin into the source test plan.

Abstract for [1500027]

    Q1: Will EPA, in consideration of difficulty in applying existing 
methods to new technology, waive the Method 5 and a portion of the 
Method 9 readings for three ship loader bustle filters at EGT 
Development, LLC's (EGT's) Export Elevator facility at Port of 
Longview, Washington?
    A1: Yes. EPA grants EGT the waiver for the Method 5 reading 
required under the initial performance and for a portion of the 
required Method 9 readings for the three bustle filters for several 
reasons. There are technical difficulties that arise in performing the 
test methods with the new loading spout dust control system design. 
Specifically, technical issues arise with conducting the Method 5 test 
where the loading spout dust control system has been moved to the 
bottom of the ship loader spout, and with conducting a Method 9 opacity 
reading while the loading spout is within the hold of the ship loading 
grain. These technical issues combined with the anticipated significant 
margin of compliance, the testing of other units with identical filter 
media at the same facility, and the opacity readings that can be 
performed justifies the waiver approval.
    Q2: Will EPA approve a waiver of initial performance testing for 
certain Donaldson bin vent CPV design PowerCore Filters (CPV filters) 
that EGT plans to install at this facility when they are in a group of 
identical units?
    A2: Yes. EPA waives the initial Method 5 performance test for 
certain CPV filters as outlined in the EPA approval letter. NSPS 
emission test results with Duraplex filter media show maximum emissions 
are an order of magnitude lower than the

[[Page 17701]]

manufacturer's guarantee (0.002 grains/dscf), and two orders of 
magnitude lower than the 0.01 grains/dscf NSPS limit. Furthermore, the 
local air permitting authority will be requiring additional testing on 
a reasonable schedule and there will be a rotation of testing within a 
group, so that a different unit within the group is tested each time 
for any future performance tests. This applies to a total of 14 NSPS 
test units, which represents a group of identical units where that 
group is unique, has a unique air volume and aspirates a conveyor or 
facility with a unique conveying capacity.

Abstract for [1500028]

    Q: Will EPA waive the requirement for Cargill Environmental Finance 
(Cargill) to performance test at two biogas-fueled generators under 
NSPS subpart JJJJ based on the test results of an identical (third) 
biogas-fueled generator at the Dry Creek Dairy in Hanson, Idaho?
    A: Yes. EPA waives the Cargill performance test for the three 
generators that are located at the same facility, produced by the same 
manufacture, have the same model number, rated capacity, operating 
specifications, and are maintained in a similar manner. There is a 
substantial margin of compliance documented by the prior performance 
test results that were submitted.

Abstract for [1500029]

    Q: Will EPA waive the requirement of 40 CFR 60.8(d) to provide 
notification 30 days in advance of a performance test for recently 
installed biogas-fueled generators at Big Sky West in Gooding, Idaho 
due to winter weather conditions and the pending holidays?
    A: Yes. EPA waives the requirement to provide notification 30 days 
in advance of a performance test pursuant to the provisions at 40 CFR 
60.19(f)(3) to implement it early in December due to weather conditions 
and the pending Holidays. EPA requests that you provide the exact 
testing date, a copy of the full testing protocol, and the results of 
the test once completed to the regulatory agencies.

Abstract for [1500030]

    Q: Does EPA determine that Shell Offshore's incineration unit 
located on the Discoverer Drill vessel, operated in the Chukchi Sea is 
exempted from the requirements of 40 CFR part 60 subpart CCCC for 
Commercial and Industrial Solid Waste Incineration Units pursuant to 
the exemption provided in 40 CFR 60.2020(c)(2)?
    A: Yes. Based on the information provided, EPA determines that 
Shell's incinerator qualifies for the exemption in 40 CFR 60.2020(c)(2) 
for units under a certain capacity that burn greater than 30 percent 
municipal solid waste or refuse-derived fuel, provided that Shell keeps 
the records required to demonstrate that it continues to qualify for 
the exemption on an ongoing basis.

Abstract for [1500031]

    Q: Does EPA determine that physical changes made to two boilers 
subject to NSPS subpart Dc owned and operated by Yakama Forest Products 
(YFP) at the Large Log Complex have de-rated the boilers' heat input 
capacity?
    A: Yes. Based on the test data submitted following the physical 
changes of replacing the burners on each boiler, EPA determines that 
boilers No. 3 and 4 have been permanently de-rated to a heat input 
capacity below 30 MM BTU/hr. YFP must ensure that oil pressure at the 
burners meets the conditions of this determination to remain consistent 
with the conditions during the source test that was the basis for this 
determination.

Abstract for [1500033]

    Q: Will EPA approve Northwest Pipeline's request for an extension 
of the deadline to conduct a performance test required by 40 CFR 
60.4340(a) in NSPS subpart KKKK for a turbine located at the Chehalis 
Compressor Station?
    A: No. EPA determines that an applicable basis for waiving the 
testing requirement has not been identified. According to 40 CFR 
60.4340(a), testing can be performed once every two years when 
emissions are less than 75 percent of the emission limit. Therefore, 
Northwest Pipeline must perform annual performance tests in accordance 
with Sec.  60.4400.

Abstract for [1500034]

    Q: Will EPA approve an alternative monitoring procedure (AMP)for 
monitoring the amount of waste combusted in the Northstar incinerator 
to demonstrate that the incinerator qualifies for the co-fired 
combustor exemption under 40 CFR part 60 subpart Ec for Hospital 
Medical Infectious Waste (HMIW) Incinerators located at BP Exploration 
Alaska's (BPXA's) Northstar Development Facility in the Beaufort Sea?
    A: No. EPA denies the AMP because use of the proposed method to 
weigh only the HMIW incinerated, instead of weighing both the HMIW and 
the non-HMIW, will not assure compliance with BPXA's claim that the 
incinerator meets the exemption for co-fired combustors under 40 CFR 
part 60 subpart Ec, as well as the exemption for ``municipal waste 
combustion units'' in 40 CFR 62.14525(c)(2).

Abstract for [1500035]

    Q: Does EPA determine that Andarko's incineration unit located at 
various drilling locations within the Gubik and Chandler Prospects in 
Alaska is exempted from the requirements of 40 CFR part 60 subpart CCCC 
pursuant to the provisions at 40 CFR 60.2020(c)(2)?
    A: Yes. Based on the information provided, EPA determines that 
Andarko's incinerator qualifies for the exemption in 40 CFR 
60.2020(c)(2) for units under a certain capacity that burn greater than 
30 percent municipal solid waste or refuse-derived fuel. Andarko must 
keep the records required to demonstrate that it continues to qualify 
for the exemption on an ongoing basis.

Abstract for [1500036]

    Q: Is fuel sampling required for two turbines owned by Black Hills 
Corporation that monitor under NSPS subpart GG custom fuel monitoring 
schedules for semi-annual periods in which the turbines have not 
operated for the entire semi-annual period? The turbines are located at 
the Glenns Ferry Cogeneration Partners and Rupert Cogeneration Partners 
facilities in Idaho.
    A: No. EPA determines that fuel sampling required by a custom fuel 
monitoring schedule is not required for semi-annual periods in which 
the turbine has not operated for the entire semi-annual period. 
Sampling must be done upon re-startup.

Abstract for [1500038]

    Q: Will EPA waive the requirement in 40 CFR 60.8(d) for Cargill to 
provide a notification 30 days in advance of a performance test for the 
recently installed biogas-fueled generators at Dry Creek Dairy in 
Hansen, Idaho?
    A: Yes. EPA waives the requirement to provide notification 30 days 
in advance of a performance test pursuant to the provisions at 40 CFR 
60.19(f)(3). The source identified a date on which testing would be 
conducted.

Abstract for [1500039]

    Q: Will EPA grant a waiver to Covanta Marion, Incorporated (CMI) in 
Brooks, Oregon, for the municipal waste combustor (MWC) unit load level 
limitations, under 40 CFR 60.53b(b)(2), for the two weeks preceding, 
and during the annual dioxin/furan and mercury performance tests for 
the purpose of evaluating system performance?

[[Page 17702]]

    A: Yes. For the purpose of evaluating system performance, EPA 
waives the MWC load limit for the two week period preceding, and during 
the annual dioxin/furan and mercury performance test.

Abstract for [1500049]

    Q: Will EPA provide a waiver pursuant to 40 CFR 60.8(b)(4) from the 
initial and subsequent performance testing requirement under NSPS 
subpart KKKK for three identical Solar Saturn T-1301 turbines operating 
under the same conditions on the same platform in the Cook Inlet at XTO 
Energy's Kenai, Alaska facility?
    A: Yes. EPA grants the request to expand the November 9, 2011 
waiver to Solar Saturn T-1301 turbine, serial number SDR-105092 under 
the condition that a different turbine will be tested each year on a 
three year rotation. If any tests exceeds 50 percent of the NOx 
emission limits, all turbines will be required to conduct performance 
tests.

Abstract for [1500051]

    Q: Can EPA approve an Alternative Monitoring Plan (AMP) for Envent 
Corporation to conduct monitoring of hydrogen sulfide (H2S) emissions, 
in lieu of installing a continuous emission monitoring system when 
performing tank degassing and other similar operations controlled by 
portable, temporary thermal oxidizers, at refineries in Region 6 States 
that are subject to NSPS subparts J or Ja?
    A: Yes. EPA conditionally approves the AMP based on the description 
of the process, the vent gas streams, the design of the vent gas 
controls, and the H2S monitoring data furnished. EPA specifies the 
proposed operating parameter limits and data which the refineries must 
furnish as part of the conditional approval. The approved AMP applies 
only to similar degassing operations conducted by ENVENT at refineries 
in EPA Region 6.

Abstract for [1500054]

    Q: Is the alternative monitoring plan (AMP) submitted to the 
Tennessee Department of Environment and Conservation (TDEC) for the 
distillation unit in Source B-99A-2 at the Eastman Chemical Company 
(Eastman) facility in Kingsport, Tennessee acceptable?
    A: Yes. Based upon the information provided in the AMP by Eastman, 
EPA determines that the AMP is acceptable since the proposed monitoring 
parameters (water flow rate, propionic acid flow rate, and propionic 
acid inlet temperature) will provide adequate assurance of compliance. 
We agree that three of the parameters that the company would be 
required to monitor under NSPS subpart NNN (propionic acid specific 
gravity, water specific gravity, and water temperature) will not be 
useful indicators of absorber performance for the source in question. 
For ongoing compliance demonstration, EPA also provides guidance on how 
to define excess emissions in terms of the alternative monitoring 
parameters.

Abstract for [1500056]

    Q1: Does a silo or frame structure enclosing a railcar loading 
station at three separate Hi-Crush Proppant nonmetallic mineral 
processing plants located in Augusta, Independence, and Blair, 
Wisconsin meet the definition of a ``building'' under NSPS subpart OOO?
    A1: Yes. Based on Hi-Crush's representation that the enclosed 
railcar loading stations are housed in structures with roofs, EPA 
concludes that these structures would meet the definition of 
``building'' in NSPS subpart OOO.
    Q2: Would the openings of those buildings be considered a ``vent''?
    A2: No. The building openings have no mechanically induced air flow 
for the purpose of exhausting from a building.
    Q3: Since these railcar loading stations are contained in a 
building, would the applicable particulate matter standard only be that 
fugitive emissions from the building openings must not exceed 7 percent 
opacity?
    A3: Yes. One emission limit option for an enclosed railcar loading 
station that is itself enclosed in a building is to restrict fugitive 
emissions from the building openings (except for vents as defined in 40 
CFR 60.671) to 7 percent opacity, per section 60.672(e)(1).

Abstract for [1500057]

    Q: Does EPA approve a waiver from the 40 part 60 subpart Ec 
requirement to monitor the minimum pressure drop across a wet scrubber 
that control emissions of acid gases (i.e., HCl) and is part of the 
emission control system for the Stericycle hospital/medical/infectious 
waste incineration (HMIWI) unit in Apopka, Florida? The Stericycle 
HMIWI unit is equipped with a dry scrubber followed by a fabric filter 
and a wet scrubber and with a selective noncatalytic reduction system. 
All other applicable parameter monitoring requirements are proposed to 
be met by the facility.
    A: Yes. EPA approves the waiver request since the removal of acid 
gases is not dependent on the monitoring of wet scrubber minimum 
pressure drop and all other applicable monitoring parameters for the 
control system will be met. Monitoring of the other wet scrubber 
monitoring parameters identified in Table 3 of subpart Ec (i.e., the 
minimum scrubber liquor flow rate and the minimum scrubber liquor pH) 
will indicate if the scrubber is working properly. Further, compliance 
with the PM emission limit is achieved without the use of the wet 
scrubber based on information.

Abstract for [1500058]

    Q: May an Alternative Monitoring Plan (AMP) be conditionally 
approved for parametric monitoring in lieu of a continuous opacity 
monitoring system (COMS) for a Wet Gas Scrubber (WGS) on a Fluidized 
Catalytic Cracking Unit (FCCU) subject to NSPS subpart J, at the 
Phillips 66 Company Alliance Refinery in Belle Chasse, Louisiana?
    A: Yes. Based on the information provided, EPA approves the AMP for 
the proposed operating parameters conditioned on the source conducting 
a performance test that demonstrates compliance and that establishes 
the operating parameter limits (OPLs) for the WGS. EPA approves the two 
proposed operating parameters, including the 1) minimum Liquid-to-Gas 
(L/G) Ratio on a 3-hour rolling average basis; and, 2) minimum slurry 
liquid circulation pump discharge pressure on a 3-hour rolling average 
basis. The OPLs are to be recalculated based on the average of three 
runs, provided the average PM emissions for the three runs meet the PM 
emissions limit of the rule in pounds per kilopounds of coke processed.

Abstract for [1500059]

    Q: Is Capitol One National Association required to petition the 
Administrator under 40 CFR 60.4211(e) for approval to exceed the 100 
hour readiness testing limit for emergency generators testing for 
commissioning purposes under subpart IIII for internal compression 
engines during the initial onsite commissioning process of its Data 
Center in Chester, Virginia?
    A: No. A petition is not necessary or appropriate. When a new 
greenfield source is under construction, subpart IIII allows emergency 
generators to be used as needed to complete the construction process, 
so long as Capitol One abides by the 100 hours limitation when the Data 
Center is in commercial operation.

Abstract for [1500060]

    Q: Portland General Electric Company (PGE) seeks verification that 
the emergency diesel-fired emergency generators at its Carver Readiness 
Center in Clackamas, Oregon, run for 50 of 100 hours total use to 
supply power,

[[Page 17703]]

allowed under NSPS subpart IIII and NESHAP subpart ZZZZ, can be part of 
its Dispatchable Standby Generation (DSG) program.
    A: 40 CFR 60.4211 and 63.6640 authorize limited non-emergency use 
of diesel engines that are classified and regulated as emergency 
engines. EPA determines that the language in 40 CFR 63.6640 of subpart 
ZZZZ regarding emergency engines dispatched under a financial 
arrangement with another entity was not intended to prohibit utilities 
from dispatching engines that they own and operate under the 50-hour 
non-emergency operation option provided.

Abstract for [1500062]

    Q: Does EPA approve revisions to the Alternative Monitoring Plan 
(AMP) for monitoring hydrogen sulfide (H2S) concentration and 
determining the total reduced sulfur (TRS) concentration in the sour 
gas routed to flares at the Lion Oil Company El Dorado (Lion Oil), 
Arkansas Refinery, which are subject to NSPS subpart Ja?
    A: Yes. EPA conditionally approves Lion Oil's revised AMP, which 
supersedes previous approvals to expand use of the approved AMP for 
determining TRS under NSPS subpart Ja, and that includes additional 
operating parameters, clarifications on sampling locations, and test 
protocol specifications.

Abstract for [1500063]

    Q: Does EPA approve a revision to an Alternative Monitoring Plan 
(AMP) that has been conditionally approved for the wet gas scrubber 
(WGS) on a Fluidized Catalytic Cracking Unit (FCCU) at Marathon 
Petroleum's refinery in Texas City, Texas subject to NSPS Part 60 
subpart J, be resubmitted for approval of a revision based on an 
additional operation mode at reduced charge rate?
    A: Yes. EPA conditionally approves the revision to the EPA-approved 
AMP based on the additional information provided by Marathon to add an 
additional mode of operation. The condition for approval requires 
Marathon to conduct performance testing to demonstrate compliance and 
to establish the operating parameter limits (OPLs) for the WGS at the 
additional FCCU reduced charge rate, as established in the EPA response 
letter.

Abstract for [1500064]

    Q: Does EPA approve alternate semiannual reporting periods under 
section 60.5420(b) of NSPS subpart OOOO to run from April 1 through 
September 30, and from October 1 through March 31, at the Atlas 
Pipeline Driver Gas Plant in Midland, Texas?
    A: Yes. EPA approves the proposed alternate reporting schedule to 
align the periodic reporting time period requirements of NSPS subpart 
0000 since it does not extend the reporting period that would be 
covered by the next semiannual report, as allowed under section 
60.5420(b). The alternate reporting schedule does not extend the 
reporting period that would be covered by the next semiannual.

Abstract for [1500065]

    Q1: Are the five City of Rock Island Public Works Department 880 HP 
spark ignition natural gas fired engines (plus one offline spare) at 
their wastewater treatment plant in Wisconsin considered emergency 
engines under NSPS subpart JJJJ?
    A1: No. Since the engines would be operated approximately 16 times 
per year for 270 hours, EPA determines that the engines do not meet the 
definition of emergency stationary internal combustion engines. 
Therefore, the engines are subject to subpart JJJJ.
    Q2: Can a waiver from performance testing be granted for the 
engines?
    A2: No. EPA cannot grant a waiver of performance testing for these 
engines, but due to the potential difficulties in testing, EPA 
encourages the City to request alternative testing if necessary.

Abstract for [1500066]

    Q: May EPA approve an alternative to stack testing under NSPS 
subpart JJJJ for nine identical non-certified Riverview bio-gas fueled 
generators located on three farms (Riverview Dairy, West River Dairy, 
and District 45 Dairy) in Minnesota?
    A: No. EPA does not approve any of the five alternative options 
proposed by Riverview for its generators, which included: (1) exemption 
from ongoing testing for engines that meet the standard, (2) 
retroactive certification by the manufacturer, (3) self-certification 
through testing, (4) provide certification to manufacturers that have 
met the standards, and (5) test one engine and apply results to all 
nine. However, EPA does provide two alternatives, Modified Option 1A 
and 1B that could be used to demonstrate compliance. Modified Option 1A 
is annual testing for NO, NOX, CO and O2 using a 
portable analyzer. Modified Option 1B is to test each dairy's engine 
sets at least once every three years, rotating annually on a three-year 
cycle.

Abstract for [1500067]

    Q: May an alternative test method be approved for Hawaiian Electric 
Company's four new compression ignition engines subject to NSPS subpart 
IIII at the Honolulu International Airport in Oahu that were certified 
on diesel but will be operated on biodiesel?
    A: Yes. EPA determines that operation of the engines on biodiesel 
would not void the certification if all of the following conditions are 
met: the biodiesel meets the requirements of 40 CFR 60.4207(b), the 
manufacturer's warranty includes the use of the biodiesel, and the 
biodiesel meets ASTM D6751. The engines must also be installed, 
configured, operated and maintained per the manufacturer's 
instructions.

Abstract for [1500068]

    Q: Does EPA approve an Alternative Monitoring Plan (AMP) for 
Evergreen Industrial Services (EIS) to conduct monitoring of hydrogen 
sulfide (H2S) emissions in lieu of installing a continuous emission 
monitoring system (CEMS), to monitor emissions controlled by portable 
and temporary thermal oxidizers units (TOUs) during tank degassing and 
other similar operations at refineries in Region 6 that are subject to 
NSPS subparts J or Ja?
    A: Yes. Based on the description of the process, the vent gas 
streams, the design of the vent gas controls, and the H2S monitoring 
data furnished, EPA conditionally approves the AMP when EIA is 
conducting degassing operations at refineries in Region 6 since it is 
impractical to use a H2S CEMS in a portable TOUs. The EPA response 
letter list the operating conditions for degassing operations and data 
which the refineries must furnish to EIS as part of the conditional 
approval.

Abstract for [1500069]

    Q: May Derenzo & Associates in Livonia, Michigan use a TECO Model 
55C analyzer in lieu of Method 18 that will be used with Method 25A to 
determine nonmethane organic compounds emitted from an internal 
combustion engine subject to NSPS subpart JJJJ?
    A: Yes. EPA approves the request to use TECO Model 55C as an 
alternative to Method 18 for measuring methane since it should produce 
results similar to the ``cutter'' analyzers already allowed by the 
regulation.

 Abstract for [1500071]

    Q: Does EPA approve the use by TRC Companies located in Lowell, 
Massachusetts of a TECO Model 55C analyzer to measure non-methane 
organic compounds (NMOC) from engines subject to NSPS subpart JJJJ?

[[Page 17704]]

    A: Yes. EPA approve TRC Companies request for use of the TECO Model 
55C analyzer in lieu of Method 18 to measure NMOC from subpart JJJJ 
engines, and the analyzer may be used by other engines subject to NSPS 
subpart JJJJ. EPA will announce this as broadly applicable to all 
stationary spark ignition combustion engines on our Web site at http://www.epa.gov/ttn/emc/trnethods.html#CatB).

 Abstract for [1500072]

    Q1: Does EPA conditionally approve a revision to a previously 
approved Alternative Monitoring Plan (AMP) to allow for an automatic 
sampling system, and an associated flow meter for collecting and 
recording hydrogen sulfide (H2S) content, to be included for the West 
Operations Ground Flare (Multi Jet Flare), which is part of a Flare Gas 
Recovery System (FGRS) subject to NSPS subpart Ja, at the Motiva 
Enterprises Norco Refinery in Norco, Louisiana?
    A1: Yes. EPA conditionally approves the AMP revision based on how 
the automatic sampling system functions regarding the configuration and 
operation of the FGRS. The H2S concentration of the combined 
refinery fuel gas stream routed to the FGRS and the Multi Jet Flare was 
less than 1 part per million. This satisfied EPA's condition for 
approval that the H2S content shall be inherently low. Additionally, 
the automatic sampling device samples the blended fuel gas stream 
before it is sent to the Multi Jet Flare, and there are no crossover 
points between the FGRS and other fuel gas streams. This satisfied 
EPA's condition for approval that no crossover points shall exist in 
the fuel gas vent stream going to the Multi Jet Flare. Based on review 
by EPA Headquarters, Motiva also was authorized to use an alternate 
test method for testing and analysis, which removed the previous 
requirement to measure and record refinery fuel gas H2S concentrations 
using the Length of Stain Tube method. EPA's ``Conditions for Approval 
of the Alternative Monitoring Plan for Miscellaneous Refinery Fuel Gas 
Streams, dated December 7, 1999, are incorporated by reference, except 
for the monitoring provisions in Steps 1 through 7, as described in the 
EPA response letter.
    Q2: What recordkeeping and report requirements are included in the 
conditional approval?
    A2: Motiva shall maintain the H2S concentration data 
from the sampling system and the alternate test method in the 
laboratory information management system. The gas flow data from the 
flow meter will be maintained in the electronic process data storage 
system. Additional records shall be kept to note when the FGRS is 
operating in either of two different scenarios. Quarterly reporting 
must be submitted, except more frequently under certain circumstances, 
as outlined in the conditional EPA approval letter.

 Abstract for [1500073]

    Q: May Derenzo & Associates in Livonia, Michigan use the TECO Model 
55I analyzer (which is a newer version of the previously approved Model 
55C) in lieu of Method 18 and Method 25A to determine non-methane 
organic compounds (NMOC) emitted from RICE subject to NSPS subpart JJJJ 
or NESHAP subpart ZZZZ?
    A: Yes. EPA approves the alternative testing request for NSPS 
subpart JJJJ, provided that the facility follows all applicable 
requirements in Method 25A for sample heating, appropriate test 
procedures, calibration and standardization. Since NESHAP subpart ZZZZ 
does not require the measurement of NMOC that part of the request is 
not considered.

 Abstract for [1500074]

    Q: Can EPA confirm the proposed deadline for completing the initial 
performance test under 40 CFR part 60 subpart Ec for the University of 
Texas Medical Branch's medical infectious waste incinerator in 
Galveston, Texas?
    A: Yes. EPA confirms that the initial compliance performance test 
should be completed within 60 days of achieving maximum production 
rate, and not later than 180 days after initial startup as required 
under section 60.8 of the General Provisions.

 Abstract for [A150001]

    Q: Does the use of the Pre-Construction Survey, as described in 
ASTM E2356-14 ``Standard Practice for Comprehensive Building Asbestos 
Surveys,'' demonstrate compliance with the ``thorough inspection'' 
requirement at 40 CFR 61.145(a)?
    A: Yes. If an owner/operator follows the steps described in 
Sections 1 through 5 and Section 8 in ASTM E2356-14 ``Standard Practice 
for Comprehensive Building Asbestos Surveys'', it would provide a 
thorough inspection of the facility. However, EPA would not accept the 
Limited Asbestos Screen (i.e., Practice E2308) described in Section 1.5 
as a substitute for the Comprehensive Building Asbestos Survey, and 
would not consider the Limited Asbestos Screen as a thorough 
inspection.

 Abstract for [C150001]

    Q: Do regulations related to ozone depleting substances under 40 
CFR part 82 prohibit the use of Leak Stop to repair leaks in 
residential air conditioning systems that contain chlorofluorocarbons?
    A: No. The use of aerosol chemical products such as Leak Stop are 
not prohibited as long as there is no ``knowing venting'' or ``knowing 
release'' of an ozone depleting substance taking place. We do not 
currently have any information about the propellant used by the Leak 
Stop product. However, if it is propelled by a Class I or II ozone 
depleting substance, then it is banned under the non-essential products 
exclusion found at 40 CFR 82.60.

 Abstract for [M150010]

    Q: Will EPA approve a waiver of the initial performance test 
according to the provisions of 40 CFR 60.8(b)(4) and 63.7(h) for a new 
chemset chamber subject to the NESHAP for Lead Acid Battery 
Manufacturing, 40 CFR part 63 subpart PPPPPP, and the NSPS for Lead 
Acid Battery Manufacturing, 40 CFR part 60 subpart KK, at the Johnson 
Controls Battery Group Inc.'s (JCBGI''s) facility in Canby, Oregon?
    A: No. EPA is denying the requested waiver because the new unit is 
not identical to the previously installed units and could have a 
different capacity. While emissions are expected to be low, the initial 
performance test is valuable to verify the installations of new 
equipment.

 Abstract for [M150011]

    Q: Will EPA approve a National Security Exemption (NSE)for the 
Department of Defense to waive the performance testing requirements for 
twelve stationary diesel fired engines constructed between 2003 and 
2009, all of which are subject to the National Emissions Standard for 
Hazardous Air Pollutants for Stationary Reciprocating Internal 
Combustion Engines (RICE) at 40 CFR part 63, subpart ZZZZ, while five 
engines are also subject to the New Source Performance Standard for 
Compression Ignition RICE at 40 CFR part 60, subpart IIII, which are 
located at Fort Greely, Alaska?
    A: No. An NSE exemption is not necessary because 40 CFR part 63 
subpart ZZZZ does not require performance testing for emergency 
engines; according, an exemption from performance testing is not 
necessary for these twelve engines if they meet the definition of 
``emergency stationary RICE'' under subpart XXXX. In addition,

[[Page 17705]]

subpart IIII does not require performance testing for manufactured-
certified engines; accordingly, an exemption from performance testing 
under subpart IIII is not necessary for the five manufactured-certified 
engines located at Fort Greely.

 Abstract for [M150012]

    Q: Does EPA determine that the operation of an emergency generator 
owned and operated by the Union Pacific Railroad's rail yard facility 
in Lane County, Oregon is classified as a stationary source under 
NESHAP subpart ZZZZ?
    A: No. EPA determines that the engine used to provide power 
restoration for emergencies at railroad tunnels in Oregon is a portable 
diesel generator. Because the engine has not provided power, or 
operated for emergency use, or any other purpose other than testing at 
the location where it has been stored for more than 12 months, it does 
not meet the definition of stationary engine for that location under 
subpart ZZZZ.

 Abstract for [M150013]

    Q1: Does EPA determine that 40 CFR part 63 subpart HHHHHH, National 
Emission Standards for Hazardous Air Pollutants: Paint Stripping and 
Miscellaneous Surface Coating Operations at Area Sources, apply to the 
process of spray applying vehicle undercoating?
    A1: Yes. EPA determines the process of spray applying vehicle 
undercoating is subject to NESHAP subpart HHHHHH. The undercoating 
would be considered a coating under the NESHAP definitions and would 
not be a sealant. It is generally spray-applied using a hand-held 
device that creates an atomized mist of coating and deposits the 
coating on a sub straight, just as are other automotive coatings.
    Q2: Does EPA determine that the exemption for facilities that do 
not spray-apply target HAP-containing coatings is available to part of 
a facility?
    A2: No. EPA determines that a facility that is not exempt must 
satisfy the rule requirements for all of their spray-applied coating 
operations. If the facility spray-applies no target HAP, then it may 
request exemption from the rule.

 Abstract for [M150015]

    Q: Will EPA approve an alternative to the visible emissions 
monitoring requirement of 40 CFR 63.11423(b) of the National Emission 
Standards for Hazardous Air Pollutants (NESHAP) for Lead Acid Battery 
Manufacturing Area Sources, subpart PPPPPP, for Johnson Controls 
Battery Group Incorporated's facility in Canby, Oregon to shut down 
equipment per permit conditions if any visible emissions are observed 
rather than continuing to operate and conduct a Method 9 test?
    A: Yes. EPA approves this minor change in monitoring methodology 
pursuant to 40 CFR 63.8(b)(i) because it will be more stringent than 
that which is required according to 40 CFR 63.11423(b) by the NESHAP 
standard.

 Abstract for [M150016]

    Q: Does 40 CFR part 63 subpart MMMMMM for Area Source Carbon Black 
Production apply to Reklaim Technologies' tire reclamation facility at 
the Port of Morrow near Boardman, Oregon?
    A: No. Based on the information provided by Reklaim, EPA determines 
that the process at Reklaim's facility is materially different from the 
``carbon black production'' process that is subject to subpart MMMMMM. 
The process involves heating shredded tires in an oxygen starved 
environment to recover carbon black, oil and steel from the tires. As 
such the process does not fall within the definition of ``carbon black 
production'' and is not subject to subpart MMMMMM.

 Abstract for [M150017]

    Q: The Olympic Region Clean Air Agency (ORCAA) in Port Angeles, 
Washington asked if 40 CFR part 63 subpart HHHHHH for Paint Stripping 
and Miscellaneous Surface Coating Operations apply to the process of 
spray-applied truck bed lining.
    A: EPA determines that operations that spray-apply coatings to 
truck bed liners, including color coatings, are subject to subpart 
HHHHHH, based on the definitions of coatings and spray-applied coating 
operations in 40 CFR 63.11180. Although the definition of ``truck bed 
liner coating'' does exclude color coats, that definition is not 
referred in 40 CFR 63.11170, the applicability section for subpart 
HHHHHH. The lining operation is generally spray-applied using a hand-
held device that creates an atomized mist of coating and deposits the 
coating on a substrate, just as are other automotive coatings.

 Abstract for [M150023]

    Q: Does EPA approve Holcim's particulate matter (PM) alternative 
continuous parameter monitoring system (CPMS) plan for the common stack 
venting exhaust emissions from different sources at their Portland 
cement plant in Florence, Colorado, subject to the National Emission 
Standards for Hazardous Air Pollutants From the Portland Cement 
Manufacturing Industry, subpart LLL?
    A: Yes. Pursuant to 40 CFR 63.8(f)(2) and 63.1350(o)(4), EPA 
conditionally approves the use of one PM CPMS on the common stack 
whereby a site-specific operating limit is established that corresponds 
to the results of performance testing demonstrating compliance with the 
kiln and clinker cooler emission limits. The conditions for approval 
are specified in the EPA response letter.

 Abstract for [M150024]

    Q: Does EPA approve an alternative monitoring plan that uses a 
longer averaging time for inlet flow monitoring as a surrogate 
parameter for monitoring methanol destruction in the Aeration 
Stabilization Basin (ASB) subject to the National Emission Standards 
for Hazardous Air Pollutants (NESHAP) from the Pulp and Paper Industry, 
subpart S, at the Clearwater Paper Corporation, Cypress Bend Mill 
located in McGehee, Arkansas?
    A: Yes. Based on the monitoring data provided by the company and 
performance test results, EPA approves the AMP request. EPA agrees that 
a daily flow is not representative of the actual hydraulic retention 
time in the ASB, whereas a nine-day rolling average inlet flow 
established per 40 CFR 63.453(n)(4) provides an actual representation 
of the treatment system retention time.

 Abstract for [M150025]

    Q: Does EPA approve an alternative monitoring request to conduct 
monthly pressure differential measurements across the catalyst at load 
conditions within plus or minus 10 percent of the baseline load 
established during the initial engine performance tests outlined in QEP 
Field Services Company's (QEP) Consent Decree, rather than the plus or 
minus 10 percent of 100 percent load as required in 40 CFR part 63 
subpart ZZZZ for Stationary Reciprocating Internal Combustion Engines 
located at Chapita, Coyote Wash, Island and Wonsits Valley Compressor 
Stations?
    A: Yes. EPA conditionally approves the AMP request pursuant to 
Sec.  63.8(t)(2) based on the performance testing negotiated as part of 
the QEP Consent Decree. EPA believes that it is technically appropriate 
to conduct the monthly pressure drop readings at plus or minus 10 
percent of the load at an affected facility engine when the initial 
performance test that was conducted is showing compliance with the MACT 
ZZZZ. The conditions for approval are described in the EPA response 
letter.

[[Page 17706]]

 Abstract for [M150026]

    Q: Do NSPS subpart IIII and NESHAP subpart ZZZZ apply to the engine 
of a mobile power generator in Springdale, Arkansas that is designed to 
supply electrical power on a temporary basis, at various locations 
within the Kawneer Springdale Plant, and does not remain at any 
location greater than 12 months?
    A: No. EPA determines that NSPS subpart IIII and NESHAP subpart 
ZZZZ do not apply since this engine is considered a nonroad mobile 
source. The mobile generator is a wheeled unit and its engine meets the 
criteria for a nonroad engine that it be by itself or in or on a piece 
of equipment that is portable or transportable. Furthermore, it will 
not remain in a single location for longer than 12 consecutive months.

 Abstract for [M150027]

    Q1: Is the stationary gas compression reciprocating internal 
combustion engine (RICE) at the Dimension Energy Company Coquille Bay, 
Louisiana facility a remote affected source under 40 CFR part 63 
subpart ZZZZ?
    A1: Yes. After reviewing the description of the RICE and its 
operations, EPA determines that it is an existing area source which 
meets the definition of a remote stationary RICE under 40 CFR 63.6675.
    Q2: What are the continuing compliance requirements for a remote 
stationary RICE?
    A2: The operator must: Perform prescribed preventative maintenance 
at certain intervals; maintain the RICE according to the manufacturer's 
instructions; minimize startup time or develop a maintenance plan using 
good air pollution prevention practices; and, maintain records to 
demonstrate that applicable requirements have been completed.

Abstract for [M150028]

    Q: Does EPA agree that the Callidus Closed Loop Gasification System 
(CCLGS) at the Del-Tin Fiber plant in El Dorado, Arkansas is exempt 
from the Boiler MACT, subpart DDDDD under the exemption at 40 CFR 
63.7491(h) because it is subject to and complying with the Plywood 
MACT, subpart DDDD?
    A: No. The EPA determines that both the Boiler MACT and the Plywood 
MACT apply to specific components of the CCLGS based on a review of the 
design and operation information available for the Del-Tin Fiber 
facility, so the exemption at 40 CFR 63.7491(h) does not apply. The 
rotary gasifiers and secondary combustion chamber (SCC) are considered 
affected sources, specifically defined as ``process heaters'' under the 
Boiler MACT when combustion gases are not used to directly heat process 
material. The portion of combustion gases that directly flow through 
the dryer units are considered affected sources under the Plywood MACT 
(Sec.  63.2232(b) and Sec.  63.2292) and are thereby exempted from the 
Boiler MACT requirements (Sec.  63.7491(1)). However, any combustion 
gases from the rotary gasifiers and the SCC that bypass the dryer units 
and are used for indirect heat transfer to process material or to heat 
transfer material for use in a process unit are subject to the Boiler 
MACT (Sec.  63.7575).

 Abstract for [M150029]

    Q: Does EPA agree to accept data from a prior performance test in 
lieu of a new performance test to demonstrate initial compliance with 
40 CFR part 63 subpart ZZZZ for six natural gas fueled spark plug 
ignition engines at the ExxonMobil Chemical facility in Baton Rouge, 
Louisiana?
    A: Yes. EPA accepts a previous performance testing for six engines 
conducted in lieu of implementing an initial test. The testing was done 
using the same methods specified in subpart ZZZZ, and was conducted 
within two years of the performance test deadline. Additionally, the 
equipment was not modified following the April 2012 testing.

 Abstract for [M150030]

    Q: Does EPA agree that the RockTenn Hodge Mill Boiler in Hodge, 
Louisiana is a biomass hybrid suspension grate boiler under 40 CFR part 
63 subpart DDDDD?
    A: Yes. EPA agrees that the boiler is subject to NESHAP subpart 
DDDDD since the description provided meets the definition of a hybrid 
suspension grate boiler found in the rule. Since natural gas and tire 
derived fuel (TDF) are also used, the facility must keep records to 
demonstrate the annual average moisture content is at or above 40 
percent. The facility must use natural gas for startup, shutdown, and 
flame stabilization, and use TDF when excessively firing wet biomass 
fuel.

 Abstract for [M150031]

    Q: Are three Electric Utility Generating Units (EUGUs) located at 
the Lafayette Utilities System (LUS) Doc Bonin Electric Generating 
Station in Lafayette, Louisiana considered to be affected sources with 
gas-fired boilers that are not subject to Boiler Area Source MACT, 
subpart JJJJJJ?
    A: EPA determines that the boilers are not affected sources subject 
to the Boiler Area Source MACT if all conditions at 40 CFR 63.11237 are 
met. Gas-fired boilers are excluded from subpart JJJJJJ per 40 CFR 
63.11195(e). A permit limitation is necessary to verify applicability 
requirements are met for each EUGU for burning fuel oil only during 
natural gas curtailment, and to not exceed testing hours with fuel oil 
during any calendar year.

 Abstract for [M150032]

    Q1: Does EPA approve an Alternative Monitoring Plan (AMP) for three 
Reciprocating Internal Combustion Engines (RICE) subject to NESHAP 
subpart ZZZZ at the Occidental Permian Terrill Gas Treating Facility 
for testing at less than 100 percent maximum load?
    A1: Yes. EPA approves Occidental Permian proposed AMP for a lower 
engine load be set as a maximum load for compliance demonstration. 
Specifically, we approve performance testing at the alternate lower 
maximum engine load with monitoring required at plus or minus 10 
percent. The three RICE cannot operate at 100 percent load due to site-
specific operations at the facility, and therefore cannot be tested at 
100 percent plus or minus 10 percent operational capacity, as specified 
at 40 CFR 63.6620(b)(2). If operations change such that the maximum 
load of the engines exceeds the alternative lower maximum load, the AMP 
approval will be terminated, and retesting will be required to 
demonstrate compliance with NESHAP subpart ZZZZ at the higher engine 
load.

 Abstract for [M150034]

    Q: Does EPA agree that the backup power generator at the Freddie 
MAC facility in Carrollton, Texas is classified as an existing 
commercial emergency stationary Reciprocating Internal Combustion 
Engine (RICE) that is not subject to 40 CFR part 63 subpart ZZZZ?
    A: Yes. EPA determines that the Freddie MAC facility is an area 
source with a commercial NAICS code, and the backup power generator 
meets the exemption provided at 40 CFR 63.6585(f)(2) applicable to 
emergency stationary RICE operated at an area source. This RICE, used 
solely for backup power generation, have not exceeded 50 hours for any 
activities during any one year period within the past two year period.

 Abstract for [M150036]

    Q: Will EPA provide a waiver to CertainTeed Corporation of the 60-
day requirement under 40 CFR 63.9(c) to notify EPA in advance of the 
initial

[[Page 17707]]

performance test at the GS Roofing facility in Portland, Oregon?
    A: Yes. EPA is granting a waiver of the 60-day requirement for a 
notification prior to the initial performance test pursuant to 40 CFR 
63.9(i) of the 40 CFR 63.9(c) requirement to enable testing during 
facility's highest volume period with the maximum ambient temperature, 
which is will occur in less than 60 days. This would enable the 
estimation of what the emissions are during a worst case scenario to 
test the limits of our system.

 Abstract for [Z150002]

    Q: Does 40 CFR part 61 subpart N apply to the Bullseye Glass 
Company's manufacture of colored art glass in its Portland, Oregon 
facility?
    A: Yes. NESHAP subpart N applies to the company's manufacture of 
colored art glass. According to 40 CFR 61.160(a), 40 CFR part 61 
subpart N does not apply to pot furnaces but rather to each glass 
melting furnace that uses commercial arsenic as a raw material. 
However, based on information provided by Bullseye Glass including 
descriptions, photos and diagrams, EPA determines that the vessels used 
by Bullseye do not meet the definition of pot furnaces because they are 
not sealed off from the furnace atmosphere so that there is potential 
for emissions to escape with the furnace exhaust.

 Abstract for [Z150004]

    Q: Are boilers/engines/marine equipment on a liquefied natural gas 
carrier (LNGC) at the proposed Aguirre Gasport located approximately 3 
miles offshore of the Puerto Rico Electric Power Authority subject to 
NSPS and NESHAP standards when the LNGC will be converted into a 
Floating Storage and Regasification Unit (FSRU) to be permanently 
moored at the GasPort?
    A: Yes. Based on the information provided, EPA determines that the 
FSRU is a stationary source because it utilizes boilers as the main 
propulsion devices instead of reciprocating internal combustion engines 
(RICE) and it will be permanently moored, except when there is a need 
to take the unit to safer water due to and special circumstances. 
Therefore, the affected equipment on the FSRU, except for non-
reciprocating internal combustion engine (RICE), is subject to NSPS and 
NESHAP standards. All non-reciprocating RICE equipment on the FSRU is 
not a stationary sources because it falls under the definition of 
nonroad engines as they will be used on self-propelled equipment. 
Therefore, the NSPS and NESHAP do not apply to the nonroad RICE. 
However, the nonroad RICE must comply with the applicable nonroad 
engine standards in 40 CFR parts 89, 94, 1039, 1042, 1043, 1045, 1048, 
1054, 1065, and 1068, if applicable. Specific questions on the 
requirements and applicability of a particular NSPS and NESHAP rules 
can be discussed separately on a case-by-case basis as the need arises.

 Abstract for [Z150005]

    Q: Are the 39 emergency stationary reciprocating internal 
combustion engines (RICE) at Los Alamos National Laboratory (LANL) area 
source facility subject to RICE NESHAP requirements?
    A: No. EPA determines that the 39 emergency RICE at LANL are not 
subject to the RICE NESHAP because they are located at an area source 
that is classified as an ``institutional'' facility. The RICE rule 
excludes existing stationary emergency engines located at residential, 
commercial, or institutional facilities that are area sources of HAP. 
Note that the engines must meet the definition of ``Emergency 
stationary RICE'' in 40 CFR 63.6675.

 Abstract for [Z150006]

    Q: Northern Natural Gas based in Omaha, Nebraska asked that, under 
40 CFR 63.6625(h), part 63 NESHAP subpart ZZZZ for spark ignition 
reciprocating internal combustion engines (RICE) regarding minimizing 
engine idle time, if an engine does not complete start up within the 
thirty minute time limit, are there any restrictions on initiating 
another startup of the engine and/or the time frame to complete the 
subsequent startup?
    A: No. An engine does not need to be shut off if it does not 
complete startup within thirty minutes. However, any further activity 
after thirty minutes is considered part of normal operation. Multiple 
startups should be counted as separate events with a thirty minute time 
limit per event. If startups occur consecutively with short durations 
in between, they could be considered as one startup since startups are 
part of a single occasion where the engine is working up to normal 
operations.

 Abstract for [Z150009]

    Q1: May emergency Reciprocating Internal Combustion Engines (RICE) 
that currently do not qualify for the exclusion in 40 CFR 63.6585(f)(2) 
because they are contractually obligated to be available for more than 
15 hours for the purposes specified at 40 CFR 63.6640(f)(2)(ii) and 
(iii) and (f)(4)(ii), later qualify for exclusion once those contracts 
expire, provided that the other conditions of 40 CFR 63.6585(f)(2) are 
met?
    A1: If an emergency stationary RICE does not meet the conditions 
for the exclusion in 40 CFR 63.6585(f)(2) as of the compliance date, 
then it is subject to subpart ZZZZ at the date of compliance. However, 
if the engine's status subsequently changes to meet the conditions of 
40 CFR 63.6585(f)(2) after the compliance date, the engine would no 
longer be subject to subpart ZZZZ.
    Q2: Can emergency RICE located at area sources continue to 
participate in peak shaving programs for up to 50 hours per year until 
May 3, 2014 without losing their emergency engine status?
    A2: An emergency stationary RICE located at an area source of HAP 
emissions can be used for peak shaving for up to 50 hours per year 
until May 3, 2014 if the engine is operated as part of a peak shaving 
(load management program) with the local distribution system operator 
and the power is provided only to the facility itself or to support the 
local distribution system. This is the case whether or not the engine 
will be retrofitted to comply with the subpart ZZZZ standards for non-
emergency engines.
    Q3: Do 40 CFR 63.6640(f)(4)(i) and (ii) address separate and 
distinct non-emergency situations, and does the ``local reliability'' 
exception set forth in 40 CFR 63.6640(f)(4)(ii) have no sunset 
provision?
    A3: Yes. 40 CFR 63.6640(f)(4)(i) and (ii) are separate and distinct 
situations and there is no sunset provision for the operation specified 
in Sec.  63.6640(f)(4)(ii). An emergency stationary RICE at an area 
source of HAP emissions can continue to operate for up to 50 hours per 
calendar year for the purpose specified in Sec.  63.6640(f)(4)(ii) 
beyond May 3, 2014.
    Q4: How does EPA interpret 40 CFR 63.6640(f)(4)(ii)(A), which 
requires that to qualify for the 50 hour exemption, the emergency RICE 
must be dispatched by the local balancing or local transmission and 
distribution system operator?
    A4: If the local transmission and distribution system operator 
informs the facility that they will be cutting their power, which, in 
turn, causes the facility to engage its emergency stationary RICE, the 
engine would be considered dispatched by the local transmission and 
distribution system operator.

 Abstract for [Z150010]

    Q1: What date is used under NESHAP subpart ZZZZ to determine if 
engines located at Allison Transmission Indianapolis facility in 
Indiana, are ``existing'' or ``new''?

[[Page 17708]]

    A1: The rule uses the date that the engine commenced construction 
to determine if the engine is existing or new. The General Provisions 
to 40 CFR part 63 define both ``construction'' and ``commenced'' and 
those definitions are applied to the subpart.
    Q2: Does NESHAP subpart ZZZZ apply to an engine that has been 
rebuilt, specifically where the engine core is reused, but components 
such as pistons, rings and bearings are reconditioned or replaced?
    A2: A rebuilt engine would need to be evaluated to determine if 
reconstruction had occurred. The General Provisions to part 63 defines 
``reconstruction.''

 Abstract for [Z150011]

    Q: Are the emergency engines located at the NASA Langley Research 
Facility in Hampton, VA subject to NESHAP subpart ZZZZ for 
Reciprocating Internal Combustion Engines?
    A: No. EPA determines that the emergency engines are located at a 
facility that is an area source and classified as an ``institutional'' 
facility. Therefore, under 40 CFR 63.6590(b)(3), emergency engines at 
the facility are exempt from requirements under NESHAP subpart ZZZZ.

 Abstract for [1600004]

    Q: Does EPA accept the industry coalition request to rescind a 
November 21, 2007, letter to the National Grain and Feed Association in 
which EPA stated that temporary storage facilities meet the definition 
of ``permanent storage capacity'' under 40 CFR part 60, subpart DD, 
NSPS for Grain Elevators (Subpart DD), and required it be included when 
determining applicability of Subpart DD for a particular facility?
    A: Yes. The EPA is proposing revisions to Subpart DD and has also 
decided to re-evaluate the rationale for the November 21, 2007 letter. 
While the definition of ``permanent storage capacity'' in Subpart DD is 
broad, we are now aware that temporary storage facilities (TSFs) 
generally handle the grain less time throughout the year than other 
types of permanent storage facilities and may require different 
treatment. Also, while not dispositive as to the applicability of the 
rule to these units, we note that TSFs did not exist during the 
development of Subpart DD, and their processes and handling techniques 
were not specifically considered during the rulemaking process. For 
these reasons, EPA rescinds the November 21, 2007 letter. As a result, 
TSFs do not meet the definition of ``permanent storage capacity'' under 
Subpart DD and should not be included when determining applicability 
under Subpart DD for a particular facility.

    Dated: February 25, 2016.
Betsy Smidinger,
Acting Director, Office of Compliance.
[FR Doc. 2016-07185 Filed 3-29-16; 8:45 am]
BILLING CODE 6560-50-P
```