Name: Edward Griegel

Title: Vice President Operations

Company: Sunbury Generation LP

Sign Date:

Name: Jeffery C. Daniels

Title: Lead Field Engineer

Company: GE International, Inc.

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, February 02, 2011 Page 1 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Facility Information:

Sunbury Generation LP

Old Trail Road

PO Box 517

Shamokin Dam PA 17876

Contact: Mark J. Crawford

Phone: 571-884-1247

Fax:

Email: mark.crawford@sunburygen.com

Testing Company:

GE International, Inc.

888 Industrial Drive

Elmhurst IL 60126

Contact:Jeffery C. Daniels

Phone: 630-530-6600

Fax: 630-530-6630

Email:

Air Permit Number: Permitted Source ID/Name:

3152 Unit 4

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Unit 4 is a 128 MW, wet bottom wall-fired bituminous coal boiler. It is equipped with Low NOx burners, over-fire 

air, flue gas conditioning, and an ESP.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4210900001 FRS #: 110000601803

SCC / Description 10100211 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Wet Bottom (Tangential) (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Unit 4 Stack 179.88 0 0 0 359.76 89.94 4 4

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Total organic compounds 

(TOC) as Propane

Unit 4 Stack Method 25A 3 180 0

Inorganic (Aqueous) 

Condensible Part.

Unit 4 Stack OTM - 27/28 3 360 0

Organic Condensible 

Particulate

Unit 4 Stack OTM - 27/28 3 360 0

Unit 4 Stack Filterable PM2.5 OTM - 27/28 3 360 0

Unit 4 Stack Filterable Particulate OTM - 27/28 3 360 0

Wednesday, February 02, 2011 Page 2 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Unit 4 Stack Total Particulate OTM - 27/28 3 360 0

Unit 4 Stack Total PM2.5 OTM - 27/28 3 360 0

Unit 4 Stack Manganese Method 29 3 240 0

Unit 4 Stack Antimony Method 29 3 240 0

Unit 4 Stack Cadmium Method 29 3 240 0

Unit 4 Stack Beryllium Method 29 3 240 0

Unit 4 Stack Chromium Method 29 3 240 0

Unit 4 Stack Lead Method 29 3 240 0

Unit 4 Stack Selenium Method 29 3 240 0

Unit 4 Stack Arsenic Method 29 3 240 0

Unit 4 Stack Nickel Method 29 3 240 0

Unit 4 Stack Cobalt Method 29 3 240 0

Unit 4 Stack Filterable Particulate Method 29 3 240 0

Wednesday, February 02, 2011 Page 3 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Sampling / Stack Data Results Summary

Location Unit 4 Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Unit 4 Stack - Method 29

Average

Run Number 1 2 3

Test Date 8/10/2010 8/11/2010 8/12/2010

Run Start Time 12:00:00 PM 9:46:00 

AM

9:17:00 AM

Run Finish Time 4:16:00 PM 2:31:00 PM 2:20:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 153.609 155.228 154.273 154.370

Moisture Content of Stack Gas, % 7.54 6.62 8.08 7.413

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11 11.3 11.1 11.133

Oxygen, % 8.1 8.1 8.1 8.100

Average Stack Gas Temperature, °F 295.73 299.92 288.92 294.857

Dry Volumetric Flow Rate, dry scfm 357,084.6 364,860.4 357,815.4 359,920.133

Actual Wet Volumetric Flue Gas Flow Rate, acfm 567,768.2 578,992.3 570,839.0 572,533.167

Percent Isokinetic of Sampling Rate, % 101.5 100.4 101.8 101.233

F-Factor, dscfm/MMBtu @ %O2 10274 10098 10080 10,150.667

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Wednesday, February 02, 2011 Page 4 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Location Unit 4 Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Wednesday, February 02, 2011 Page 5 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Emissions Summary

Location: Unit 4 Stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 6.36E-04 1.32E-03 1.18E-03 0.001

ppm 3.38E-01 6.88E-01 6.05E-01 0.544

ppm@7%O2 3.70E-01 7.59E-01 6.73E-01 0.601

Location: Unit 4 Stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.01 0.01 0.01 0.010

lb/mmBtuO2 2.41E-06 2.34E-06 2.35E-06 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.02293 0.02423 0.03483 0.027

lb/mmBtuO2 5.52E-06 5.67E-06 8.19E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.0025 0.0025 0.00271 0.003

lb/mmBtuO2 6.02E-07 5.85E-07 6.37E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0025 0.0025 0.0025 0.003

lb/mmBtuO2 6.02E-07 5.85E-07 5.88E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.01979 0.03092 0.02359 0.025

lb/mmBtuO2 4.76E-06 7.24E-06 5.55E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00347 0.00334 0.00449 0.004

lb/mmBtuO2 8.35E-07 7.82E-07 1.06E-06 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 56.2 58.7 99.2 71.367

lb/mmBtuO2 1.35E-02 1.37E-02 2.33E-02 0.017

Wednesday, February 02, 2011 Page 6 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.01206 0.01206 0.01346 0.013

lb/mmBtuO2 2.90E-06 2.82E-06 3.17E-06 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.02214 0.02854 0.03154 0.027

lb/mmBtuO2 5.33E-06 6.68E-06 7.42E-06 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0212 0.0359 0.0203 0.026

lb/mmBtuO2 5.10E-06 8.41E-06 4.77E-06 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.1111 0.1393 0.1129 0.121

lb/mmBtuO2 2.67E-05 3.26E-05 2.66E-05 0.000

Location: Unit 4 Stack - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 43.7 27.9 52.8 41.467

lb/mmBtuO2 1.16E-02 7.54E-03 1.43E-02 0.011

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 10.4 7.2 14.9 10.833

lb/mmBtuO2 2.76E-03 1.95E-03 4.03E-03 0.003

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 22.9 25.2 36.4 28.167

lb/mmBtuO2 6.07E-03 6.81E-03 9.84E-03 0.008

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 4.7 5.4 5.3 5.133

lb/mmBtuO2 1.25E-03 1.46E-03 1.43E-03 0.001

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 71.3 58.5 94.5 74.767

Wednesday, February 02, 2011 Page 7 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Process Run Data

lb/mmBtuO2 1.89E-02 1.58E-02 2.55E-02 0.020

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 38 37.8 56.6 44.133

lb/mmBtuO2 1.01E-02 1.02E-02 1.53E-02 0.012

Wednesday, February 02, 2011 Page 8 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 48.2 Tons/hr Collected during 

run 1 M29

0

1 Steam Flow 953 KPPH Collected during 

run 1 M29

0

1 Daily Avg. Stack Pressure 14.34 psia Collected during 

run 1 M29

0

1 Daily Avg. Stack Temp 285.1 degrees F Collected during 

run 1 M29

0

1 SO2 CEMS 2.928 lb/mmbtu Collected during 

run 1 M29

0

1 NOx CEMS 0.286 lb/mmbtu Collected during 

run 1 M29

0

1 Gross Generation 3039 MW Collected during 

run 1 M29

0

1 Net Generation 2777 MW Collected during 

run 1 M29

0

1 Daily Avg. Fuel Flow 1 gal/day Collected during 

run 1 M29

0

1 Daily Avg. Stack Flow 56.86 ft/sec Collected during 

run 1 M29

0

1 Daily Avg. CO2 10.3 % Collected during 

run 1 M29

0

1 Boiler O2 - A1 2.457 % Collected during 

run 1 M29

0

2 Bituminous Coal Burned 59.9 Tons/hr Collected during 

run 2 M29

0

2 Steam Flow 961 KPPH Collected during 

run 2 M29

0

2 Daily Avg. Stack Pressure 14.32 psia Collected during 

run 2 M29

0

2 Daily Avg. Stack Temp 294 degrees F Collected during 

run 2 M29

0

2 SO2 CEMS 3.249 lb/mmbtu Collected during 

run 2 M29

0

2 NOx CEMS 0.261 lb/mmbtu Collected during 

run 2 M29

0

2 Gross Generation 3055 MW Collected during 

run 2 M29

0

2 Net Generation 2792 MW Collected during 

run 2 M29

0

2 Daily Avg. Fuel Flow 0 gal/day Collected during 

run 2 M29

0

Wednesday, February 02, 2011 Page 9 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

2 Daily Avg. Stack Flow 56.74 ft/sec Collected during 

run 2 M29

0

2 Daily Avg. CO2 10.3 % Collected during 

run 2 M29

0

2 Boiler O2 - A1 2.21 % Collected during 

run 2 M29

0

3 Bituminous Coal Burned 56.1 Tons/hr Collected during 

run 3 M29

0

3 Steam Flow 947 KPPH Collected during 

run 3 M29

0

3 Daily Avg. Stack Pressure 14.31 psia Collected during 

run 3 M29

0

3 Daily Avg. Stack Temp 284 degrees F Collected during 

run 3 M29

0

3 SO2 CEMS 3.156 lb/mmbtu Collected during 

run 3 M29

0

3 NOx CEMS 0.279 lb/mmbtu Collected during 

run 3 M29

0

3 Gross Generation 3002 MW Collected during 

run 3 M29

0

3 Net Generation 2743 MW Collected during 

run 3 M29

0

3 Daily Avg. Fuel Flow 0 gal/day Collected during 

run 3 M29

0

3 Daily Avg. Stack Flow 56.56 ft/sec Collected during 

run 3 M29

0

3 Daily Avg. CO2 10.2 % Collected during 

run 3 M29

0

3 Boiler O2 - A1 2.657 % Collected during 

run 3 M29

0

4 Bituminous Coal Burned 48.2 Tons/hr Collected during 

run 1 OTM 27/28

0

4 Steam Flow 949 KPPH Collected during 

run 1 OTM 27/28

0

4 Daily Avg. Stack Pressure 14.34 psia Collected during 

run 1 OTM 27/28

0

4 Daily Avg. Stack Temp 285.1 degrees F Collected during 

run 1 OTM 27/28

0

4 SO2 CEMS 2.937 lb/mmbtu Collected during 

run 1 OTM 27/28

0

4 NOx CEMS 0.286 lb/mmbtu Collected during 

run 1 OTM 27/28

0

4 Gross Generation 3039 MW Collected during 

run 1 OTM 27/28

0

4 Net Generation 2777 MW Collected during 

run 1 OTM 27/28

0

Wednesday, February 02, 2011 Page 10 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

4 Daily Avg. Fuel Flow 1 gal/day Collected during 

run 1 OTM 27/28

0

4 Daily Avg. Stack Flow 56.86 ft/sec Collected during 

run 1 OTM 27/28

0

4 Daily Avg. CO2 10.3 % Collected during 

run 1 OTM 27/28

0

4 Boiler O2 - A1 2.45 % Collected during 

run 1 OTM 27/28

0

5 Bituminous Coal Burned 59.9 Tons/hr Collected during 

run 2 OTM 27/28

0

5 Steam Flow 961 KPPH Collected during 

run 2 OTM 27/28

0

5 Daily Avg. Stack Pressure 14.32 psia Collected during 

run 2 OTM 27/28

0

5 Daily Avg. Stack Temp 294 degrees F Collected during 

run 2 OTM 27/28

0

5 SO2 CEMS 3.241 lb/mmbtu Collected during 

run 2 OTM 27/28

0

5 NOx CEMS 0.263 lb/mmbtu Collected during 

run 2 OTM 27/28

0

5 Gross Generation 3055 MW Collected during 

run 2 OTM 27/28

0

5 Net Generation 2792 MW Collected during 

run 2 OTM 27/28

0

5 Daily Avg. Fuel Flow 0 gal/day Collected during 

run 2 OTM 27/28

0

5 Daily Avg. Stack Flow 56.74 ft/sec Collected during 

run 2 OTM 27/28

0

5 Daily Avg. CO2 10.3 % Collected during 

run 2 OTM 27/28

0

5 Boiler O2 - A1 2.151 % Collected during 

run 2 OTM 27/28

0

6 Bituminous Coal Burned 56.1 Tons/hr Collected during 

run 3 OTM 27/28

0

6 Steam Flow 948 KPPH Collected during 

run 3 OTM 27/28

0

6 Daily Avg. Stack Pressure 14.31 psia Collected during 

run 3 OTM 27/28

0

6 Daily Avg. Stack Temp 284 degrees F Collected during 

run 3 OTM 27/28

0

6 SO2 CEMS 3.144 lb/mmbtu Collected during 

run 3 OTM 27/28

0

6 NOx CEMS 0.277 lb/mmbtu Collected during 

run 3 OTM 27/28

0

6 Gross Generation 3002 MW Collected during 

run 3 OTM 27/28

0

Wednesday, February 02, 2011 Page 11 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

6 Net Generation 2743 MW Collected during 

run 3 OTM 27/28

0

6 Daily Avg. Fuel Flow 0 gal/day Collected during 

run 3 OTM 27/28

0

6 Daily Avg. Stack Flow 56.56 ft/sec Collected during 

run 3 OTM 27/28

0

6 Daily Avg. CO2 10.2 % Collected during 

run 3 OTM 27/28

0

6 Boiler O2 - A1 2.593 % Collected during 

run 3 OTM 27/28

0

7 Bituminous Coal Burned 52.5 Tons/hr Collected during 

run 1 M25A

0

7 Steam Flow 940 KPPH Collected during 

run 1 M25A

0

7 Daily Avg. Stack Pressure 14.39 psia Collected during 

run 1 M25A

0

7 Daily Avg. Stack Temp 276.4 degrees F Collected during 

run 1 M25A

0

7 SO2 CEMS 3.157 lb/mmbtu Collected during 

run 1 M25A

0

7 NOx CEMS 0.258 lb/mmbtu Collected during 

run 1 M25A

0

7 Gross Generation 2885 MW Collected during 

run 1 M25A

0

7 Net Generation 2630 MW Collected during 

run 1 M25A

0

7 Daily Avg. Fuel Flow 337 gal/day Collected during 

run 1 M25A

0

7 Daily Avg. Stack Flow 54.62 ft/sec Collected during 

run 1 M25A

0

7 Daily Avg. CO2 10 % Collected during 

run 1 M25A

0

7 Boiler O2 - A1 3.708 % Collected during 

run 1 M25A

0

8 Bituminous Coal Burned 52.5 Tons/hr Collected during 

run 2 M25A

0

8 Steam Flow 937 KPPH Collected during 

run 2 M25A

0

8 Daily Avg. Stack Pressure 14.39 psia Collected during 

run 2 M25A

0

8 Daily Avg. Stack Temp 276.4 degrees F Collected during 

run 2 M25A

0

8 SO2 CEMS 3.158 lb/mmbtu Collected during 

run 2 M25A

0

8 NOx CEMS 0.257 lb/mmbtu Collected during 

run 2 M25A

0

Wednesday, February 02, 2011 Page 12 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

8 Gross Generation 2885 MW Collected during 

run 2 M25A

0

8 Net Generation 2630 MW Collected during 

run 2 M25A

0

8 Daily Avg. Fuel Flow 337 gal/day Collected during 

run 2 M25A

0

8 Daily Avg. Stack Flow 54.62 ft/sec Collected during 

run 2 M25A

0

8 Daily Avg. CO2 10 % Collected during 

run 2 M25A

0

8 Boiler O2 - A1 3.708 % Collected during 

run 2 M25A

0

9 Bituminous Coal Burned 52.5 Tons/hr Collected during 

run 3 M25A

0

9 Steam Flow 929 KPPH Collected during 

run 3 M25A

0

9 Daily Avg. Stack Pressure 14.39 psia Collected during 

run 3 M25A

0

9 Daily Avg. Stack Temp 276.4 degrees F Collected during 

run 3 M25A

0

9 SO2 CEMS 3.116 lb/mmbtu Collected during 

run 3 M25A

0

9 NOx CEMS 0.264 lb/mmbtu Collected during 

run 3 M25A

0

9 Gross Generation 2885 MW Collected during 

run 3 M25A

0

9 Net Generation 2630 MW Collected during 

run 3 M25A

0

9 Daily Avg. Fuel Flow 337 gal/day Collected during 

run 3 M25A

0

9 Daily Avg. Stack Flow 54.62 ft/sec Collected during 

run 3 M25A

0

9 Daily Avg. CO2 10 % Collected during 

run 3 M25A

0

9 Boiler O2 - A1 3.708 % Collected during 

run 3 M25A

0

1 Boiler O2 - A2 3.031 % Collected during 

run 1 M29

0

2 Boiler O2 - A2 3.117 % Collected during 

run 2 M29

0

3 Boiler O2 - A2 3.79 % Collected during 

run 3 M29

0

4 Boiler O2 - A2 3.044 % Collected during 

run 1 OTM 27/28

0

5 Boiler O2 - A2 3.15 % Collected during 

run 2 OTM 27/28

0

Wednesday, February 02, 2011 Page 13 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

6 Boiler O2 - A2 3.749 % Collected during 

run 3 OTM 27/28

0

7 Boiler O2 - A2 3.942 % Collected during 

run 1 M25A

0

8 Boiler O2 - A2 3.942 % Collected during 

run 2 M25A

0

9 Boiler O2 - A2 3.942 % Collected during 

run 3 M25A

0

1 Boiler O2 - B1 3.69 % Collected during 

run 1 M29

0

2 Boiler O2 - B1 3.411 % Collected during 

run 2 M29

0

3 Boiler O2 - B1 3.168 % Collected during 

run 3 M29

0

4 Boiler O2 - B1 3.676 % Collected during 

run 1 OTM 27/28

0

5 Boiler O2 - B1 3.422 % Collected during 

run 2 OTM 27/28

0

6 Boiler O2 - B1 3.139 % Collected during 

run 3 OTM 27/28

0

7 Boiler O2 - B1 3.565 % Collected during 

run 1 M25A

0

8 Boiler O2 - B1 3.565 % Collected during 

run 2 M25A

0

9 Boiler O2 - B1 3.565 % Collected during 

run 3 M25A

0

1 Boiler O2 - B2 2.722 % Collected during 

run 1 M29

0

2 Boiler O2 - B2 2.992 % Collected during 

run 2 M29

0

3 Boiler O2 - B2 3.404 % Collected during 

run 3 M29

0

4 Boiler O2 - B2 2.717 % Collected during 

run 1 OTM 27/28

0

5 Boiler O2 - B2 3.097 % Collected during 

run 2 OTM 27/28

0

6 Boiler O2 - B2 3.396 % Collected during 

run 3 OTM 27/28

0

7 Boiler O2 - B2 3.497 % Collected during 

run 1 M25A

0

8 Boiler O2 - B2 3.497 % Collected during 

run 2 M25A

0

9 Boiler O2 - B2 3.497 % Collected during 

run 3 M25A

0

1 Heat Input 1435 MMBtu/hr Collected during 

run 1 M29

0

Wednesday, February 02, 2011 Page 14 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

APCD Run Data

Process Lab Run Data

2 Heat Input 1448 MMBtu/hr Collected during 

run 2 M29

0

3 Heat Input 1437 MMBtu/hr Collected during 

run 3 M29

0

4 Heat Input 1465 MMBtu/hr Collected during 

run 1 OTM 27/28

0

5 Heat Input 1450 MMBtu/hr Collected during 

run 2 OTM 27/28

0

6 Heat Input 1440 MMBtu/hr Collected during 

run 3 OTM 27/28

0

7 Heat Input 1472 MMBtu/hr Collected during 

run 1 M25A

0

8 Heat Input 1411 MMBtu/hr Collected during 

run 2 M25A

0

9 Heat Input 1442 MMBtu/hr Collected during 

run 3 M25A

0

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 0 0

1 OVERFIRE AIR 0 0

1 FLUE GAS RECIRCULATION 0 0

1 ELECTROSTATIC PRECIPITATOR 0 0

Wednesday, February 02, 2011 Page 15 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Sampling / Stack Data Results Detail

Location Unit 4 Stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Wednesday, February 02, 2011 Page 16 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Location Unit 4 Stack - Method 29

Average

Run Number 1 2 3

Test Date 8/10/2010 8/11/2010 8/12/2010

Run Start Time 12:00:00 PM 9:46:00 AM 9:17:00 AM

Run Finish Time 4:16:00 PM 2:31:00 PM 2:20:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.239 0.239 0.239 0.239

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.994 0.994 0.994 0.994

Barometric Pressure, inches of Mercury 29.15 29.08 28.96 29.063

Average Orifice Meter Differential, inches H2O 1.29 1.33 1.27 1.297

Dry Gas Meter Volume Sampled, cubic feet 168.183 170.841 166.088 168.371

Average Dry Gas Meter Temperature, °F 101.66 103.29 88.66 97.870

Dry Gas Meter Volume Sampled, dscf 153.609 155.228 154.273 154.370

Total Moisture Liquid collected, g 266 233.6 288.1 262.567

Volume of Water Vapor, standard cubic feet 12.52 11.00 13.56 12.360

Moisture Content of Stack Gas, % 7.54 6.62 8.08 7.413

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9246 0.9338 0.9192 0.926

Carbon Dioxide, % 11 11.3 11.1 11.133

Oxygen, % 8.1 8.1 8.1 8.100

Carbon Monoxide & Nitrogen, % 80.9 80.6 80.8 80.767

Fuel Factor 1.16 1.13 1.15

Dry Molecular Weight, lb/lb-Mole 30.08 30.13 30.10 30.103

Wet Molecular weight, lb/lb-Mole 29.17 29.33 29.12 29.207

Flue Gas Static Pressure, inches of H2O -0.3 -0.3 -0.3 -0.300

Absolute Flue Gas Pressure, inches of Mercury 29.13 29.06 28.94 29.043

Average Stack Gas Temperature, °F 295.73 299.92 288.92 294.857

Average Velocity Head, inches of H2O 0.6269153250

3664

0.650177995

667963

0.634060204

437105

0.637

Average Stack Gas Velocity, feet/second 53.62 54.68 53.91 54.070

Stack Cross-Sectional Area, square feet 176.479 176.479 176.479 176.479

Dry Volumetric Flow Rate, dry scfm 357,084.6 364,860.4 357,815.4 359,920.133

Actual Wet Volumetric Flue Gas Flow Rate, acfm 567,768.2 578,992.3 570,839.0 572,533.167

Percent Isokinetic of Sampling Rate, % 101.5 100.4 101.8 101.233

Percent Excess Air, % 61.1 61.5 61.2 61.267

F-Factor, dscfm/MMBtu @ %O2 10274 10098 10080 10,150.667

Round Duct Diameter, inches 179.88 179.88 179.88

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Wednesday, February 02, 2011 Page 17 of 18
Utility Boiler MACT ICR - Sunbury Power Plant Unit 4

Location Unit 4 Stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Wednesday, February 02, 2011 Page 18 of 18