# Wisconsin Power and Light Company

Edgewater-Unit 4 Hg CEMs Data VoluntarilyProvided to Supplement Hg/HAPICR Data Response On April2, 2010, WisconsinPowerand Light Company (“WPL”)submitted its electronic response to the Utility MACT (Hg/HAP) Information CollectionRequest (ICR). WPLvoluntarilysubmitted withits response a mercury continuous emission monitoring s (“CEMS”) report for EdgewaterUnit 4. WPLsubmitted that report in Adobe PDF format.WPLis augmenting its originalrespons this Excel formatof the CEMS data at the specific request of Mr. Bill Maxwell,U.S.EnvironmentalProtectionAgency

.WPLco the PDF version that it submitted on April 2, 2010 to be its official submittal.

The CEMSdata in this file is for the period of 01/01/2009

-12/31/2009.Start date of the time period for which Hg CEMS data i availablereflects post

-installationand QA/QC of the Tekran continuous mercury emission monitor system for EdgewaterUnit 4. T is no applicableCAMR,state or NIST QA/QC procedure applicableto the operationand maintenance of the Tekran continuous mer emission monitors. The mercury CEMs data includes a legendwhichidentifies periods of start

-up, shut

WPLnotes that the mercury emission control system on EdgewaterUnit 4 (calcium bromide injection) became operationalin Dece 2009.

# On April2, 2010, WisconsinPowerand Light Company (“WPL”)submitted its electronic response to the Utility MACT (Hg/HAP) Information CollectionRequest (ICR). WPLvoluntarilysubmitted withits response a mercury continuous emission monitoring system (“CEMS”) report for EdgewaterUnit 4. WPLsubmitted that report in Adobe PDF format.WPLis augmenting its originalresponse with this Excel formatof the CEMS data at the specific request of Mr. Bill Maxwell,U.S.EnvironmentalProtectionAgency

.WPLconsiders

12/31/2009.Start date of the time period for which Hg CEMS data is installationand QA/QC of the Tekran continuous mercury emission monitor system for EdgewaterUnit 4. There is no applicableCAMR,state or NIST QA/QC procedure applicableto the operationand maintenance of the Tekran continuous mercury up, shut

-downandmalfunction events.

WPLnotes that the mercury emission control system on EdgewaterUnit 4 (calcium bromide injection) became operationalin December

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 C 16:00 C 17:00 C 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 2.8 3.4 01/02/09 33,051,580.0 274.51,840.02,371.1 239 60.00 2.435 0.092 4.1 01/02/09 35,543,576.0 280.2 1,840.02,569.2 259 60.00 2.935 0.121 4.2 01/02/09 40,261,600.0 282.51,840.02,954.0 296 60.00 3.487 0.165 4.0 01/02/09 39,473,500.0 281.3 1,840.02,874.7 290 60.00 3.599 0.165 3.7 01/02/09 38,095,216.0 278.51,840.02,774.3 278 60.00 3.427 0.152 3.7 01/02/09 33,794,028.0 271.4 1,840.02,406.0 238 60.00 3.243 0.125 3.3 01/02/09 26,042,940.0 267.0 1,840.0 1,811.7 185 60.00 3.319 0.096 3.6 01/02/09 27,522,502.0 269.9 1,840.0 1,914.6 199 60.00 2.960 0.091 3.7 01/02/09 27,586,782.0 270.51,840.0 1,904.1 196 60.00 3.255 0.099 3.9 01/02/09 28,630,618.0 270.2 1,840.0 1,991.7 203 60.00 3.319 0.106 3.5 01/02/09 27,262,304.0 269.2 1,840.0 1,866.9 196 60.00 3.554 0.106 3.8 01/02/09 28,218,004.0 270.6 1,840.0 1,978.3 206 60.00 3.115 0.099 4.3 01/02/09 28,332,172.0 269.2 1,840.0 1,986.3 204 60.00 3.382 0.107 4.1 01/01/09 27,105,934.0 268.4 1,840.0 1,915.1 194 60.00 3.798 0.116 4.2 01/01/09 28,305,240.0 272.7 1,840.0 1,999.8 207 60.00 3.621 0.116 4.6 01/01/09 36,146,616.0 281.7 1,840.02,612.8 264 60.00 3.626 0.151 4.6 01/01/09 40,774,020.0 282.6 1,840.02,947.3 297 60.00 3.971 0.187 5.2 01/01/09 40,327,564.0 280.4 1,840.02,936.9 295 60.00 3.941 0.185 5.5 01/01/09 39,359,800.0 279.8 1,840.02,887.8 289 60.00 4.423 0.204 4.4 01/01/09 40,367,796.0 281.1 1,840.02,939.8 293 60.00 4.713 0.222 3.6 01/01/09 35,139,480.0 270.4 1,840.02,578.1 249 60.00 3.742 0.154 4.1 01/01/09 27,890,660.0 265.9 1,840.02,000.9 201 60.00 3.131 0.100 4.4 01/01/09 27,852,044.0 267.4 1,840.0 1,982.9 198 60.00 3.593 0.114 4.2 01/01/09 31,161,714.0 270.9 1,840.02,252.5 221 60.00 3.798 0.137 4.2 01/01/09 32,467,076.0 271.7 1,840.02,364.4 233 60.00 3.599 0.136 4.2 01/01/09 36,468,296.0 278.4 1,840.02,655.8 266 60.00 3.599 0.153 4.3 01/01/09 37,601,324.0 274.3 1,840.02,738.3 268 60.00 3.599 0.158 4.7 01/01/09 31,173,576.0 270.8 1,840.02,202.5 220 60.00 3.798 0.134 3.8 01/01/09 32,616,348.0 268.8 1,840.02,339.8 231 60.00 4.088 0.153 3.7 01/01/09 27,930,782.0 265.51,840.0 1,927.8 196 60.00 3.435 0.106 3.9 01/01/09 27,061,822.0 265.1 1,840.0 1,853.2 188 60.00 3.372 0.100 5.5 01/01/09 26,311,584.0 264.7 1,840.0 1,801.8 184 60.00 3.554 0.102 5.1 01/01/09 26,801,058.0 265.2 1,840.0 1,849.9 192 60.00 4.972 0.147 4.8 01/01/09 27,835,380.0 264.51,840.0 1,921.2 198 60.00 4.611 0.142 3.9 01/01/09 26,039,002.0 266.1 1,840.0 1,811.4 184 60.00 4.306 0.125 5.6 01/01/09 27,298,458.0 272.9 1,840.0 1,913.8 199 60.00 3.471 0.106 2,825.8 278 60.00 4.763 01/01/09 38,514,676.0 281.6 1,840.0 0.215 

### HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 3.9 3.6 01/04/09 31,762,226.0 271.3 1,840.02,278.6 224 60.00 3.392 0.124 3.6 01/04/09 27,556,118.0 271.1 1,840.0 1,946.9 197 60.00 3.180 0.099 4.2 01/03/09 32,457,948.0 277.1 1,840.02,363.8 235 60.00 3.085 0.117 4.5 01/03/09 37,774,044.0 283.4 1,840.02,771.5 276 60.00 3.572 0.158 4.7 01/03/09 40,464,728.0 284.1 1,840.02,968.9 295 60.00 3.827 0.182 4.7 01/03/09 40,348,184.0 283.4 1,840.02,960.3 297 60.00 3.997 0.189 4.4 01/03/09 40,509,336.0 283.6 1,840.02,972.1 298 60.00 3.997 0.190 4.3 01/03/09 40,774,272.0 284.1 1,840.02,991.6 298 60.00 3.742 0.179 3.2 01/03/09 40,985,648.0 284.1 1,840.03,007.1 299 60.00 3.657 0.176 3.3 01/03/09 38,130,140.0 279.9 1,840.02,776.9 270 60.00 2.742 0.122 3.3 01/03/09 37,037,472.0 279.2 1,840.02,737.5 268 60.00 2.786 0.122 3.2 01/03/09 37,025,616.0 279.2 1,840.02,736.7 268 60.00 2.786 0.122 3.2 01/03/09 37,865,520.0 280.3 1,840.02,778.2 275 60.00 2.722 0.121 3.2 01/03/09 37,744,268.0 280.7 1,840.02,789.8 274 60.00 2.702 0.121 3.0 01/03/09 38,894,332.0 280.2 1,840.02,874.8 283 60.00 2.702 0.124 3.7 01/03/09 37,447,232.0 280.1 1,840.02,747.5 271 60.00 2.551 0.112 4.0 01/03/09 39,243,940.0 282.2 1,840.02,836.7 282 60.00 3.194 0.145 3.5 01/03/09 40,478,516.0 282.3 1,840.02,969.9 294 60.00 3.402 0.162 4.0 01/03/09 35,177,136.0 275.1 1,840.02,580.9 251 60.00 2.977 0.123 3.7 01/03/09 30,584,482.0 270.0 1,840.02,194.1 214 60.00 3.479 0.122 4.5 01/03/09 27,136,488.0 269.6 1,840.0 1,917.2 194 60.00 3.268 0.100 4.6 01/03/09 29,863,700.0 275.2 1,840.02,158.6 218 60.00 3.885 0.134 4.1 01/03/09 34,786,728.0 277.3 1,840.02,552.3 251 60.00 3.912 0.160 5.0 01/03/09 34,507,488.0 276.7 1,840.02,531.8 255 60.00 3.487 0.141 5.4 01/03/09 37,644,412.0 281.51,840.02,761.9 277 60.00 4.252 0.188 3.1 01/03/09 40,141,104.0 283.2 1,840.02,923.3 294 60.00 4.627 0.216 4.0 01/02/09 38,868,732.0 277.9 1,840.02,872.9 280 60.00 2.617 0.120 5.2 01/02/09 32,714,280.0 276.3 1,840.02,400.2 239 60.00 3.402 0.131 5.4 01/02/09 37,703,280.0 282.6 1,840.02,766.3 276 60.00 4.423 0.196 4.8 01/02/09 40,653,288.0 283.51,840.03,004.8 299 60.00 4.559 0.219 4.7 01/02/09 40,583,836.0 283.4 1,840.02,999.7 299 60.00 4.052 0.194 3.5 01/02/09 40,690,496.0 282.1 1,840.03,007.5 298 60.00 3.968 0.191 3.2 01/02/09 36,817,052.0 277.7 1,840.02,701.2 267 60.00 2.977 0.129 3.7 01/02/09 33,828,960.0 275.7 1,840.02,463.6 245 60.00 2.742 0.108 3.2 01/02/09 34,731,088.0 276.6 1,840.02,510.4 250 60.00 3.194 0.128 3.0 01/02/09 36,276,276.0 277.6 1,840.02,641.8 261 60.00 2.742 0.116 01/02/09 34,481,408.0 273.8 1,840.02,492.4 248 60.00 2.590 0.103

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 3.2 3.1 01/05/09 40,495,016.0 283.51,840.03,015.1 299 60.00 2.682 0.129 3.4 01/05/09 40,624,036.0 284.1 1,840.03,024.7 299 60.00 2.598 0.126 3.3 01/05/09 40,639,812.0 284.6 1,840.03,003.8 299 60.00 2.870 0.138 3.1 01/05/09 40,587,816.0 284.51,840.03,000.0 299 60.00 2.786 0.134 2.9 01/05/09 40,369,684.0 283.6 1,840.03,005.8 299 60.00 2.598 0.125 3.1 01/05/09 40,217,896.0 282.7 1,840.02,994.5 299 60.00 2.430 0.116 3.9 01/05/09 40,487,224.0 283.6 1,840.03,014.5 299 60.00 2.598 0.125 4.1 01/05/09 40,648,704.0 283.8 1,840.03,026.6 300 60.00 3.268 0.158 2.7 01/05/09 40,158,620.0 279.2 1,840.02,990.1 293 60.00 3.436 0.164 2.9 01/05/09 31,629,004.0 271.0 1,840.02,303.4 227 60.00 2.313 0.085 2.8 01/05/09 33,403,666.0 277.4 1,840.02,450.8 249 60.00 2.466 0.097 2.3 01/05/09 39,422,492.0 278.3 1,840.02,913.8 288 60.00 2.364 0.110 3.1 01/05/09 32,913,780.0 272.4 1,840.02,379.1 230 60.00 1.986 0.076 2.7 01/05/09 31,728,418.0 273.6 1,840.02,276.1 227 60.00 2.696 0.098 2.0 01/05/09 28,488,844.0 269.3 1,840.02,059.3 205 60.00 2.331 0.077 4.3 01/04/09 28,955,462.0 273.4 1,840.02,108.7 211 60.00 1.714 0.058 4.9 01/04/09 35,782,368.0 282.9 1,840.02,625.3 262 60.00 3.657 0.154 4.9 01/04/09 40,807,428.0 284.9 1,840.03,038.3 299 60.00 4.107 0.200 4.9 01/04/09 40,323,480.0 284.1 1,840.03,002.3 297 60.00 4.107 0.197 4.3 01/04/09 40,396,140.0 283.4 1,840.02,985.8 299 60.00 4.137 0.198 4.1 01/04/09 40,434,668.0 282.51,840.03,010.6 298 60.00 3.604 0.173 4.4 01/04/09 39,265,480.0 282.4 1,840.02,880.9 287 60.00 3.487 0.161 4.7 01/04/09 40,610,004.0 283.8 1,840.02,979.5 297 60.00 3.742 0.178 4.4 01/04/09 40,809,316.0 284.3 1,840.02,994.1 298 60.00 3.997 0.191 4.0 01/04/09 40,297,552.0 283.6 1,840.03,000.4 297 60.00 3.688 0.177 3.9 01/04/09 40,208,192.0 282.7 1,840.02,971.9 295 60.00 3.377 0.160 4.0 01/04/09 40,966,984.0 283.8 1,840.03,005.7 299 60.00 3.317 0.159 4.3 01/04/09 40,513,328.0 282.0 1,840.02,972.4 294 60.00 3.402 0.162 4.3 01/04/09 39,050,532.0 282.7 1,840.02,822.7 282 60.00 3.712 0.168 3.9 01/04/09 38,819,900.0 278.1 1,840.02,869.3 277 60.00 3.630 0.167 4.1 01/04/09 31,106,854.0 274.8 1,840.02,231.6 218 60.00 3.392 0.121 4.1 01/04/09 33,438,990.0 274.2 1,840.02,417.1 234 60.00 3.539 0.137 3.7 01/04/09 29,727,602.0 268.7 1,840.02,116.5 210 60.00 3.593 0.122 3.6 01/04/09 27,400,106.0 268.1 1,840.0 1,921.0 194 60.00 3.293 0.101 3.4 01/04/09 30,898,346.0 272.9 1,840.02,199.8 220 60.00 3.155 0.111 3.7 01/04/09 30,756,470.0 271.9 1,840.02,189.7 215 60.00 2.980 0.104 01/04/09 30,438,458.0 274.51,840.02,150.5 216 60.00 3.268 0.112

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 2.8 3.2 01/07/09 26,906,186.0 271.2 1,840.0 1,886.3 187 60.00 2.492 0.075 3.0 01/07/09 33,392,376.0 277.4 1,840.02,413.7 241 60.00 2.762 0.107 3.2 01/07/09 34,988,960.0 275.9 1,840.02,529.1 251 60.00 2.590 0.105 2.2 01/07/09 34,789,124.0 277.1 1,840.02,514.6 248 60.00 2.762 0.111 2.8 01/06/09 33,936,316.0 276.2 1,840.02,471.4 240 60.00 1.885 0.074 2.7 01/06/09 35,705,532.0 281.2 1,840.02,580.9 259 60.00 2.417 0.100 3.0 01/06/09 38,381,548.0 282.2 1,840.02,816.1 282 60.00 2.296 0.103 3.3 01/06/09 39,311,568.0 284.0 1,840.02,862.9 288 60.00 2.571 0.118 3.2 01/06/09 40,139,804.0 285.4 1,840.02,923.2 295 60.00 2.828 0.132 3.1 01/06/09 40,644,052.0 285.6 1,840.02,982.0 299 60.00 2.722 0.130 3.1 01/06/09 40,349,064.0 285.0 1,840.02,960.4 299 60.00 2.637 0.125 3.2 01/06/09 40,230,612.0 284.3 1,840.02,951.7 297 60.00 2.637 0.124 3.3 01/06/09 40,050,064.0 284.3 1,840.02,938.5 293 60.00 2.722 0.128 3.2 01/06/09 39,624,808.0 284.51,840.02,885.7 290 60.00 2.828 0.130 3.4 01/06/09 39,987,364.0 284.7 1,840.02,912.1 294 60.00 2.742 0.128 4.0 01/06/09 40,547,748.0 284.1 1,840.02,975.0 299 60.00 2.892 0.138 3.6 01/06/09 40,397,184.0 284.7 1,840.02,963.9 297 60.00 3.402 0.161 3.4 01/06/09 40,082,392.0 284.51,840.02,919.0 294 60.00 3.085 0.144 3.2 01/06/09 40,664,868.0 283.7 1,840.02,961.5 297 60.00 2.913 0.138 3.4 01/06/09 39,351,696.0 282.3 1,840.02,887.2 290 60.00 2.722 0.126 2.9 01/06/09 40,372,580.0 282.2 1,840.02,984.1 298 60.00 2.870 0.137 2.7 01/06/09 40,468,844.0 282.1 1,840.02,991.2 297 60.00 2.448 0.117 2.1 01/06/09 38,570,716.0 278.8 1,840.02,829.9 280 60.00 2.296 0.104 2.2 01/06/09 34,092,668.0 271.9 1,840.02,445.8 238 60.00 1.827 0.071 2.6 01/06/09 28,167,804.0 269.4 1,840.02,020.7 202 60.00 1.914 0.062 2.9 01/06/09 30,206,322.0 271.6 1,840.02,117.7 211 60.00 2.314 0.078 2.9 01/06/09 32,111,410.0 273.8 1,840.02,286.2 228 60.00 2.542 0.093 2.6 01/06/09 34,719,920.0 278.8 1,840.02,490.8 251 60.00 2.522 0.100 2.6 01/05/09 36,691,616.0 276.3 1,840.02,712.0 262 60.00 2.195 0.095 3.3 01/05/09 34,117,044.0 278.1 1,840.02,521.7 248 60.00 2.195 0.089 3.4 01/05/09 37,078,848.0 281.51,840.02,760.8 269 60.00 2.766 0.122 3.2 01/05/09 40,100,744.0 284.9 1,840.02,942.2 291 60.00 2.892 0.136 3.1 01/05/09 41,151,252.0 284.51,840.03,019.2 299 60.00 2.722 0.131 3.0 01/05/09 40,631,732.0 284.0 1,840.02,981.2 299 60.00 2.637 0.126 3.0 01/05/09 40,731,444.0 284.4 1,840.03,010.6 299 60.00 2.533 0.122 3.1 01/05/09 40,688,092.0 284.7 1,840.03,007.4 298 60.00 2.533 0.122 01/05/09 40,969,608.0 284.8 1,840.03,006.0 298 60.00 2.637 0.127

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 3.5 3.6 01/08/09 38,939,124.0 281.7 1,840.02,856.9 284 60.00 2.977 0.136 3.6 01/08/09 39,055,304.0 283.2 1,840.02,844.2 285 60.00 3.085 0.140 3.7 01/08/09 39,279,112.0 283.3 1,840.02,881.9 286 60.00 3.062 0.141 4.3 01/08/09 39,376,084.0 283.6 1,840.02,867.6 286 60.00 3.170 0.145 4.3 01/08/09 40,289,112.0 284.51,840.02,956.0 296 60.00 3.657 0.173 4.2 01/08/09 40,389,560.0 283.4 1,840.02,941.4 298 60.00 3.684 0.173 4.2 01/08/09 40,606,488.0 283.3 1,840.02,935.1 299 60.00 3.626 0.170 3.9 01/08/09 40,589,580.0 283.1 1,840.02,956.0 299 60.00 3.599 0.170 3.5 01/08/09 41,095,208.0 282.6 1,840.02,948.1 299 60.00 3.392 0.160 3.1 01/08/09 38,170,180.0 275.9 1,840.02,759.0 276 60.00 3.021 0.133 2.9 01/08/09 31,762,254.0 270.6 1,840.02,226.8 223 60.00 2.759 0.098 2.6 01/08/09 29,781,146.0 267.8 1,840.02,039.4 203 60.00 2.643 0.086 2.7 01/08/09 25,552,822.0 266.8 1,840.0 1,763.7 172 60.00 2.351 0.066 2.5 01/08/09 27,017,562.0 268.8 1,840.0 1,879.5 188 60.00 2.422 0.073 2.7 01/08/09 28,782,432.0 269.6 1,840.02,033.5 198 60.00 2.208 0.072 3.3 01/08/09 29,491,602.0 273.51,840.02,083.7 209 60.00 2.385 0.079 3.5 01/08/09 35,171,380.0 280.2 1,840.02,542.3 253 60.00 2.849 0.116 3.4 01/07/09 38,984,232.0 281.0 1,840.02,839.1 281 60.00 2.999 0.136 3.5 01/07/09 38,779,340.0 283.2 1,840.02,739.8 275 60.00 3.003 0.132 3.9 01/07/09 39,550,568.0 283.9 1,840.02,858.8 287 60.00 3.021 0.138 3.9 01/07/09 41,001,132.0 285.7 1,840.02,985.9 299 60.00 3.342 0.160 3.8 01/07/09 40,995,864.0 286.2 1,840.02,985.6 298 60.00 3.342 0.160 3.9 01/07/09 41,573,620.0 287.1 1,840.03,005.1 299 60.00 3.280 0.158 3.7 01/07/09 40,531,784.0 285.1 1,840.02,951.8 298 60.00 3.342 0.158 3.5 01/07/09 38,705,764.0 281.0 1,840.02,818.8 283 60.00 3.170 0.143 3.3 01/07/09 37,410,852.0 280.7 1,840.02,724.5 273 60.00 2.999 0.131 3.3 01/07/09 38,056,788.0 282.51,840.02,792.2 279 60.00 2.807 0.125 3.5 01/07/09 38,368,868.0 283.51,840.02,794.3 280 60.00 2.828 0.126 3.4 01/07/09 40,384,864.0 284.6 1,840.02,941.1 295 60.00 2.999 0.141 3.6 01/07/09 40,004,808.0 284.3 1,840.02,913.4 291 60.00 2.913 0.136 3.6 01/07/09 40,295,320.0 283.7 1,840.02,912.6 296 60.00 3.108 0.145 3.4 01/07/09 40,595,348.0 283.1 1,840.02,934.3 297 60.00 3.108 0.146 3.1 01/07/09 40,355,188.0 281.3 1,840.02,917.0 295 60.00 2.935 0.137 2.8 01/07/09 38,636,516.0 278.4 1,840.02,792.8 278 60.00 2.676 0.120 2.6 01/07/09 32,069,776.0 270.3 1,840.02,265.8 222 60.00 2.473 0.090 2.6 01/07/09 27,401,886.0 268.4 1,840.0 1,936.0 190 60.00 2.296 0.071 01/07/09 25,920,928.0 268.0 1,840.0 1,831.4 179 60.00 2.296 0.067

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 3.7 3.5 01/10/09 32,217,116.0 274.1 1,840.02,328.7 231 60.00 3.194 0.119 3.4 01/10/09 28,818,430.0 268.2 1,840.02,036.1 193 60.00 3.091 0.101 4.2 01/10/09 24,564,988.0 269.4 1,840.0 1,682.2 170 60.00 3.098 0.083 3.7 01/10/09 29,689,890.0 273.9 1,840.02,049.3 210 60.00 3.797 0.124 3.3 01/10/09 31,626,676.0 270.9 1,840.02,268.9 224 60.00 3.218 0.117 3.3 01/10/09 25,813,910.0 268.51,840.0 1,809.8 183 60.00 2.937 0.085 4.0 01/09/09 28,716,256.0 273.51,840.02,060.1 208 60.00 2.870 0.095 3.7 01/09/09 35,645,364.0 280.9 1,840.02,615.3 262 60.00 3.402 0.142 3.7 01/09/09 40,166,732.0 283.7 1,840.02,947.0 294 60.00 3.147 0.148 3.7 01/09/09 38,619,952.0 282.51,840.02,833.5 281 60.00 3.147 0.143 3.4 01/09/09 39,548,108.0 283.9 1,840.02,901.6 286 60.00 3.147 0.146 3.3 01/09/09 40,004,596.0 284.1 1,840.02,935.1 294 60.00 2.892 0.136 3.2 01/09/09 40,156,720.0 284.51,840.03,011.8 298 60.00 2.746 0.132 3.1 01/09/09 39,174,656.0 282.7 1,840.02,959.4 290 60.00 2.643 0.125 2.9 01/09/09 38,696,968.0 282.1 1,840.02,923.3 286 60.00 2.561 0.120 3.3 01/09/09 39,050,640.0 283.1 1,840.02,928.8 285 60.00 2.413 0.113 3.7 01/09/09 39,375,860.0 284.2 1,840.02,953.2 288 60.00 2.746 0.130 3.6 01/09/09 40,366,432.0 284.51,840.02,983.6 293 60.00 3.124 0.149 3.6 01/09/09 40,757,280.0 285.51,840.03,034.6 299 60.00 3.017 0.146 3.4 01/09/09 40,973,092.0 285.3 1,840.03,006.2 300 60.00 3.062 0.147 3.5 01/09/09 41,035,712.0 285.0 1,840.02,966.2 299 60.00 2.935 0.139 3.0 01/09/09 40,672,088.0 283.7 1,840.03,006.2 299 60.00 2.955 0.142 2.3 01/09/09 39,284,496.0 280.6 1,840.02,882.3 288 60.00 2.551 0.118 2.5 01/09/09 36,105,440.0 275.1 1,840.02,629.4 260 60.00 1.971 0.083 1.4 01/09/09 29,545,844.0 269.9 1,840.02,135.7 209 60.00 2.158 0.074 2.2 01/09/09 28,345,012.0 268.4 1,840.02,033.4 200 60.00 1.218 0.040 2.6 01/09/09 25,736,548.0 269.4 1,840.0 1,804.4 182 60.00 1.958 0.056 2.9 01/09/09 29,253,958.0 272.4 1,840.02,019.2 203 60.00 2.351 0.076 3.2 01/09/09 32,274,106.0 277.51,840.02,350.4 234 60.00 2.485 0.093 2.3 01/09/09 37,351,268.0 280.3 1,840.02,801.3 275 60.00 2.662 0.119 2.9 01/08/09 37,430,552.0 281.51,840.02,787.0 275 60.00 1.928 0.086 3.1 01/08/09 38,402,888.0 283.51,840.02,859.4 282 60.00 2.430 0.111 3.5 01/08/09 40,000,924.0 285.3 1,840.02,956.6 293 60.00 2.617 0.124 4.0 01/08/09 40,370,144.0 285.0 1,840.03,005.8 299 60.00 2.933 0.141 4.0 01/08/09 40,374,524.0 284.7 1,840.02,984.2 298 60.00 3.377 0.161 4.0 01/08/09 40,841,064.0 285.2 1,840.03,018.7 300 60.00 3.377 0.163 01/08/09 40,736,156.0 284.51,840.02,988.8 299 60.00 3.402 0.163

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 4.2 4.0 01/11/09 40,326,380.0 284.8 1,840.03,024.5 299 60.00 3.494 0.169 3.6 01/11/09 40,388,496.0 283.9 1,840.03,007.1 299 60.00 3.352 0.161 3.7 01/11/09 37,974,576.0 279.9 1,840.02,827.5 278 60.00 3.017 0.136 4.2 01/11/09 35,034,732.0 279.0 1,840.02,570.5 254 60.00 3.147 0.129 5.1 01/11/09 36,315,984.0 281.7 1,840.02,664.5 264 60.00 3.572 0.152 5.2 01/11/09 39,649,496.0 284.51,840.02,909.0 289 60.00 4.337 0.202 5.0 01/11/09 38,698,860.0 283.6 1,840.02,881.4 284 60.00 4.358 0.201 4.4 01/11/09 39,108,296.0 282.4 1,840.02,911.8 288 60.00 4.190 0.195 4.3 01/11/09 36,301,788.0 280.6 1,840.02,683.2 266 60.00 3.715 0.159 4.5 01/11/09 39,028,452.0 283.0 1,840.02,905.9 290 60.00 3.604 0.167 4.7 01/11/09 37,799,216.0 281.9 1,840.02,834.9 280 60.00 3.744 0.170 4.5 01/11/09 37,861,752.0 282.4 1,840.02,819.1 280 60.00 3.939 0.178 4.5 01/11/09 37,384,076.0 280.2 1,840.02,824.1 276 60.00 3.717 0.168 5.1 01/11/09 34,539,752.0 279.1 1,840.02,534.2 253 60.00 3.827 0.155 5.2 01/11/09 38,054,044.0 282.8 1,840.02,792.0 278 60.00 4.337 0.194 5.2 01/11/09 38,868,416.0 283.2 1,840.02,830.6 284 60.00 4.456 0.202 5.0 01/11/09 39,254,048.0 283.2 1,840.02,858.7 289 60.00 4.456 0.204 4.8 01/11/09 38,535,712.0 282.7 1,840.02,827.4 283 60.00 4.252 0.192 3.6 01/11/09 37,795,040.0 281.6 1,840.02,773.0 275 60.00 4.082 0.181 4.7 01/10/09 37,425,272.0 281.4 1,840.02,745.9 272 60.00 3.062 0.134 5.0 01/10/09 39,296,816.0 283.8 1,840.02,883.2 289 60.00 3.997 0.184 5.1 01/10/09 39,934,168.0 284.9 1,840.02,929.9 294 60.00 4.252 0.199 5.0 01/10/09 40,470,524.0 285.3 1,840.02,969.3 296 60.00 4.337 0.206 5.1 01/10/09 40,430,520.0 285.0 1,840.02,966.4 298 60.00 4.252 0.202 5.3 01/10/09 40,546,640.0 285.6 1,840.02,974.9 299 60.00 4.337 0.206 5.3 01/10/09 40,639,496.0 284.9 1,840.02,959.6 299 60.00 4.541 0.215 5.1 01/10/09 39,351,012.0 282.9 1,840.02,865.8 289 60.00 4.541 0.208 5.4 01/10/09 39,293,344.0 283.3 1,840.02,861.6 290 60.00 4.370 0.200 5.4 01/10/09 38,985,568.0 283.4 1,840.02,839.2 287 60.00 4.627 0.210 4.7 01/10/09 39,467,892.0 283.51,840.02,852.9 289 60.00 4.662 0.213 4.9 01/10/09 39,806,024.0 283.8 1,840.02,898.9 293 60.00 4.027 0.187 3.7 01/10/09 40,102,872.0 283.0 1,840.02,942.3 297 60.00 4.167 0.196 4.0 01/10/09 39,978,696.0 284.1 1,840.02,955.0 297 60.00 3.124 0.148 4.0 01/10/09 40,256,108.0 284.4 1,840.02,997.3 297 60.00 3.352 0.161 4.2 01/10/09 39,261,976.0 282.4 1,840.02,902.0 287 60.00 3.377 0.157 4.1 01/10/09 37,986,300.0 281.8 1,840.02,807.7 278 60.00 3.546 0.159 01/10/09 37,484,036.0 277.3 1,840.02,790.9 272 60.00 3.436 0.153

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 4.6 4.3 01/13/09 40,135,920.0 283.1 1,840.02,988.4 296 60.00 3.855 0.184 3.4 01/13/09 37,140,364.0 276.8 1,840.02,785.5 270 60.00 3.578 0.159 4.1 01/13/09 30,201,774.0 270.4 1,840.02,183.1 213 60.00 2.935 0.102 4.4 01/13/09 27,856,506.0 273.2 1,840.0 1,998.4 200 60.00 3.566 0.114 4.6 01/13/09 31,092,014.0 272.1 1,840.02,213.6 217 60.00 3.856 0.137 5.0 01/13/09 25,580,486.0 266.9 1,840.0 1,793.4 173 60.00 4.094 0.117 3.7 01/13/09 25,022,940.0 269.4 1,840.0 1,767.9 180 60.00 4.416 0.125 2.3 01/13/09 26,852,316.0 267.51,840.0 1,926.3 190 60.00 3.218 0.099 3.1 01/12/09 23,442,510.0 266.9 1,840.0 1,656.3 164 60.00 2.031 0.054 3.3 01/12/09 28,056,822.0 272.9 1,840.02,012.8 204 60.00 2.696 0.087 3.1 01/12/09 33,583,716.0 276.0 1,840.02,445.8 240 60.00 2.828 0.111 4.0 01/12/09 33,902,636.0 280.2 1,840.02,469.0 245 60.00 2.656 0.105 3.7 01/12/09 39,640,304.0 285.3 1,840.02,908.4 290 60.00 3.402 0.158 3.2 01/12/09 40,647,648.0 284.9 1,840.03,004.4 300 60.00 3.124 0.150 3.3 01/12/09 40,020,980.0 284.4 1,840.02,979.8 298 60.00 2.682 0.128 3.3 01/12/09 39,020,272.0 283.0 1,840.02,905.3 288 60.00 2.766 0.128 4.0 01/12/09 38,048,868.0 283.0 1,840.02,833.0 280 60.00 2.766 0.125 4.7 01/12/09 39,320,072.0 284.8 1,840.02,949.0 292 60.00 3.328 0.157 4.7 01/12/09 38,954,416.0 285.1 1,840.02,921.6 289 60.00 3.910 0.183 4.2 01/12/09 40,045,136.0 286.1 1,840.03,003.4 297 60.00 3.910 0.188 3.7 01/12/09 39,524,144.0 284.8 1,840.02,985.8 295 60.00 3.469 0.166 3.3 01/12/09 39,172,936.0 284.1 1,840.02,938.0 294 60.00 3.078 0.145 3.5 01/12/09 39,655,116.0 283.8 1,840.02,995.7 299 60.00 2.726 0.131 3.7 01/12/09 39,978,244.0 284.6 1,840.03,020.1 299 60.00 2.891 0.140 3.4 01/12/09 38,449,456.0 280.7 1,840.02,862.8 283 60.00 3.101 0.142 3.0 01/12/09 30,993,392.0 271.2 1,840.02,257.1 218 60.00 2.913 0.105 3.1 01/12/09 25,513,612.0 266.9 1,840.0 1,816.5 180 60.00 2.629 0.076 3.2 01/12/09 24,594,136.0 268.4 1,840.0 1,724.3 173 60.00 2.759 0.076 3.9 01/12/09 25,877,610.0 271.3 1,840.0 1,800.2 184 60.00 2.870 0.083 3.9 01/12/09 31,550,434.0 274.2 1,840.02,194.8 226 60.00 3.498 0.123 3.4 01/12/09 31,053,144.0 274.7 1,840.02,227.7 228 60.00 3.392 0.121 3.2 01/12/09 34,397,256.0 277.1 1,840.02,505.0 252 60.00 2.913 0.117 3.7 01/11/09 34,061,884.0 280.3 1,840.02,499.1 250 60.00 2.722 0.109 3.5 01/11/09 39,230,508.0 283.9 1,840.02,899.7 290 60.00 3.124 0.145 3.9 01/11/09 39,450,544.0 284.1 1,840.02,915.9 292 60.00 2.955 0.138 4.1 01/11/09 40,072,328.0 283.8 1,840.02,983.6 300 60.00 3.268 0.156 01/11/09 40,084,396.0 284.3 1,840.03,006.3 298 60.00 3.411 0.164

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 C 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 4.4 4.4 01/14/09 40,858,200.0 286.2 1,840.03,042.1 299 60.00 3.688 0.179 4.5 01/14/09 40,732,468.0 286.1 1,840.03,032.8 299 60.00 3.688 0.179 4.4 01/14/09 40,477,812.0 285.1 1,840.03,013.9 299 60.00 3.771 0.182 4.3 01/14/09 40,446,784.0 284.7 1,840.03,011.5 299 60.00 3.688 0.178 4.4 01/14/09 40,637,780.0 285.0 1,840.03,025.8 299 60.00 3.604 0.174 4.4 01/14/09 40,283,564.0 284.1 1,840.02,977.5 294 60.00 3.715 0.177 4.2 01/14/09 38,965,000.0 282.4 1,840.02,880.0 284 60.00 3.715 0.171 4.7 01/14/09 40,241,744.0 284.6 1,840.02,952.5 294 60.00 3.572 0.169 4.9 01/14/09 40,667,116.0 284.9 1,840.02,983.7 297 60.00 3.997 0.191 4.7 01/14/09 41,073,760.0 285.4 1,840.03,013.6 300 60.00 4.167 0.201 4.7 01/14/09 40,913,420.0 284.9 1,840.03,001.8 300 60.00 3.997 0.192 4.5 01/14/09 40,374,172.0 283.4 1,840.02,962.2 299 60.00 3.997 0.189 5.0 01/14/09 40,669,124.0 284.0 1,840.02,983.9 300 60.00 3.827 0.183 5.1 01/14/09 39,733,804.0 284.7 1,840.02,915.3 291 60.00 4.252 0.198 4.9 01/14/09 40,614,852.0 284.6 1,840.03,024.1 298 60.00 4.274 0.207 4.7 01/14/09 38,763,200.0 280.1 1,840.02,907.2 284 60.00 4.077 0.190 4.5 01/14/09 36,128,120.0 279.9 1,840.02,690.0 263 60.00 3.939 0.169 4.9 01/14/09 37,020,776.0 279.6 1,840.02,736.3 267 60.00 3.799 0.166 5.0 01/14/09 37,789,092.0 282.8 1,840.02,772.6 276 60.00 4.167 0.185 4.6 01/14/09 39,317,744.0 281.51,840.02,948.8 290 60.00 4.160 0.196 4.4 01/14/09 35,689,232.0 277.9 1,840.02,676.7 261 60.00 3.827 0.164 4.8 01/13/09 36,185,364.0 280.2 1,840.02,694.2 264 60.00 3.688 0.159 5.1 01/13/09 37,468,364.0 283.9 1,840.02,789.7 275 60.00 4.023 0.179 5.3 01/13/09 40,029,204.0 285.7 1,840.02,980.4 295 60.00 4.274 0.204 5.2 01/13/09 40,162,296.0 285.2 1,840.03,012.2 299 60.00 4.410 0.212 5.2 01/13/09 40,101,472.0 284.3 1,840.03,007.6 299 60.00 4.326 0.208 5.5 01/13/09 40,700,036.0 285.3 1,840.03,030.4 300 60.00 4.358 0.211 5.2 01/13/09 40,789,888.0 285.4 1,840.03,059.3 299 60.00 4.576 0.224 5.4 01/13/09 38,759,872.0 282.9 1,840.02,907.0 282 60.00 4.326 0.201 5.3 01/13/09 39,124,076.0 283.6 1,840.02,955.6 289 60.00 4.460 0.211 5.2 01/13/09 40,605,140.0 285.1 1,840.03,045.4 299 60.00 4.410 0.215 4.9 01/13/09 40,214,720.0 284.3 1,840.03,016.1 294 60.00 4.326 0.209 4.2 01/13/09 39,256,840.0 284.2 1,840.02,944.3 288 60.00 4.077 0.192 4.2 01/13/09 40,266,156.0 284.4 1,840.02,998.1 299 60.00 3.520 0.169 3.3 01/13/09 40,260,356.0 283.1 1,840.02,997.6 299 60.00 3.520 0.169 4.9 01/13/09 39,885,860.0 283.0 1,840.02,969.8 296 60.00 2.766 0.131 01/13/09 39,738,700.0 283.1 1,840.02,937.2 293 60.00 4.137 0.194

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 C 02:00 C C 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 4.7 4.7 01/16/09 40,937,064.0 282.8 1,840.03,048.0 299 60.00 3.939 0.192 4.3 01/16/09 40,896,664.0 281.4 1,840.03,067.3 300 60.00 3.910 0.192 3.4 01/16/09 40,736,332.0 278.2 1,840.03,055.2 299 60.00 3.578 0.175 3.4 01/16/09 36,136,236.0 271.8 1,840.02,690.6 260 60.00 2.849 0.123 3.5 01/16/09 32,297,338.0 270.51,840.02,352.1 229 60.00 2.913 0.110 3.8 01/16/09 31,651,146.0 273.7 1,840.02,356.6 228 60.00 2.933 0.111 5.9 01/16/09 37,302,068.0 278.9 1,840.02,777.4 274 60.00 3.185 0.141 4.0 01/16/09 37,004,880.0 277.3 1,840.02,755.3 266 60.00 4.945 0.218 3.9 01/16/09 35,657,028.0 279.3 1,840.02,674.3 260 60.00 3.328 0.142 4.0 01/16/09 38,300,016.0 280.51,840.02,893.3 283 60.00 3.221 0.149 4.1 01/15/09 39,186,692.0 283.3 1,840.02,939.0 289 60.00 3.328 0.156 4.3 01/15/09 40,992,204.0 285.0 1,840.03,052.1 299 60.00 3.436 0.168 4.3 01/15/09 40,992,340.0 284.7 1,840.03,052.1 300 60.00 3.604 0.176 4.0 01/15/09 40,671,116.0 283.8 1,840.03,028.2 300 60.00 3.604 0.175 4.2 01/15/09 40,686,560.0 284.7 1,840.03,029.4 299 60.00 3.352 0.162 4.3 01/15/09 40,828,200.0 285.1 1,840.03,039.9 300 60.00 3.520 0.171 4.4 01/15/09 40,922,696.0 285.1 1,840.03,024.7 299 60.00 3.630 0.176 4.3 01/15/09 40,449,844.0 284.6 1,840.03,011.8 299 60.00 3.688 0.178 3.6 01/15/09 40,327,032.0 283.2 1,840.03,024.5 297 60.00 3.578 0.173 3.3 01/15/09 40,267,736.0 283.7 1,840.02,998.2 296 60.00 3.017 0.145 3.4 01/15/09 40,283,644.0 283.6 1,840.02,977.5 294 60.00 2.786 0.133 3.3 01/15/09 40,678,496.0 284.4 1,840.03,028.7 299 60.00 2.849 0.138 3.3 01/15/09 40,271,104.0 283.8 1,840.03,020.3 299 60.00 2.746 0.133 3.2 01/15/09 40,010,824.0 283.3 1,840.03,044.3 300 60.00 2.706 0.132 3.4 01/15/09 40,000,296.0 283.9 1,840.03,043.5 298 60.00 2.624 0.128 3.3 01/15/09 40,270,260.0 284.1 1,840.03,042.1 299 60.00 2.808 0.137 3.2 01/15/09 40,393,236.0 284.9 1,840.03,051.4 299 60.00 2.726 0.133 2.8 01/15/09 40,259,656.0 281.51,840.03,063.3 298 60.00 2.624 0.129 3.2 01/15/09 35,523,948.0 277.3 1,840.02,702.9 262 60.00 2.296 0.099 2.8 01/15/09 35,735,624.0 280.4 1,840.02,699.6 263 60.00 2.643 0.114 2.9 01/15/09 40,067,240.0 283.7 1,840.03,048.6 298 60.00 2.296 0.112 3.5 01/15/09 39,507,928.0 283.3 1,840.02,941.6 292 60.00 2.430 0.114 3.6 01/15/09 40,522,168.0 284.4 1,840.02,995.1 297 60.00 2.955 0.142 2.7 01/15/09 40,162,472.0 284.51,840.02,990.3 295 60.00 3.017 0.144 3.7 01/14/09 40,045,732.0 283.1 1,840.03,003.5 295 60.00 2.246 0.108 4.0 01/14/09 39,304,056.0 282.7 1,840.02,947.8 289 60.00 3.078 0.145 01/14/09 39,436,436.0 284.4 1,840.02,936.3 289 60.00 3.352 0.157

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 4.3 4.2 01/17/09 36,831,852.0 278.2 1,840.02,742.4 267 60.00 3.604 0.158 4.5 01/17/09 35,418,728.0 278.8 1,840.02,637.2 259 60.00 3.520 0.148 4.4 01/17/09 38,318,168.0 281.7 1,840.02,811.4 279 60.00 3.827 0.172 4.2 01/17/09 39,191,884.0 281.3 1,840.02,875.5 286 60.00 3.742 0.172 4.1 01/17/09 38,345,736.0 279.8 1,840.02,813.4 279 60.00 3.572 0.161 3.7 01/17/09 35,161,212.0 275.1 1,840.02,560.6 252 60.00 3.513 0.144 3.7 01/17/09 30,437,202.0 271.1 1,840.02,133.9 212 60.00 3.293 0.112 4.2 01/17/09 30,338,610.0 274.7 1,840.02,160.0 216 60.00 3.243 0.112 4.5 01/17/09 33,745,980.0 277.6 1,840.02,475.9 245 60.00 3.572 0.141 4.6 01/17/09 37,124,452.0 281.3 1,840.02,723.8 273 60.00 3.827 0.167 4.9 01/17/09 39,255,428.0 283.3 1,840.02,880.1 288 60.00 3.912 0.180 5.0 01/17/09 39,329,632.0 283.9 1,840.02,885.6 288 60.00 4.167 0.192 5.1 01/17/09 39,528,604.0 283.7 1,840.02,900.2 291 60.00 4.252 0.197 4.6 01/17/09 40,222,132.0 283.3 1,840.02,972.9 296 60.00 4.306 0.205 3.6 01/17/09 38,306,936.0 276.9 1,840.02,810.6 276 60.00 3.912 0.176 4.2 01/17/09 30,225,564.0 271.3 1,840.02,201.2 211 60.00 3.085 0.109 3.8 01/17/09 30,202,636.0 274.1 1,840.02,166.7 215 60.00 3.653 0.127 3.4 01/17/09 31,644,732.0 268.8 1,840.02,287.4 218 60.00 3.280 0.120 3.8 01/17/09 24,479,298.0 266.7 1,840.0 1,716.2 169 60.00 3.026 0.083 4.3 01/17/09 25,746,460.0 272.51,840.0 1,805.0 182 60.00 3.382 0.098 4.8 01/17/09 34,071,636.0 279.1 1,840.02,499.8 250 60.00 3.657 0.146 4.8 01/17/09 38,389,756.0 282.1 1,840.02,858.4 282 60.00 4.023 0.184 3.9 01/17/09 38,136,804.0 281.51,840.02,839.5 279 60.00 4.023 0.183 5.0 01/16/09 39,765,732.0 283.3 1,840.02,960.8 291 60.00 3.268 0.155 4.9 01/16/09 39,248,052.0 281.3 1,840.02,922.3 286 60.00 4.190 0.196 4.8 01/16/09 39,093,628.0 282.0 1,840.02,910.8 288 60.00 4.107 0.191 4.8 01/16/09 39,595,184.0 283.2 1,840.02,969.6 291 60.00 3.994 0.190 4.6 01/16/09 40,728,288.0 283.6 1,840.03,032.5 298 60.00 4.023 0.195 4.5 01/16/09 40,349,336.0 283.7 1,840.03,004.2 295 60.00 3.855 0.185 3.9 01/16/09 39,493,676.0 281.7 1,840.02,962.1 290 60.00 3.744 0.177 4.0 01/16/09 38,456,404.0 279.8 1,840.02,884.2 282 60.00 3.245 0.150 4.3 01/16/09 38,003,604.0 281.6 1,840.02,829.6 277 60.00 3.352 0.152 4.2 01/16/09 39,328,020.0 283.1 1,840.02,928.2 286 60.00 3.604 0.169 4.4 01/16/09 40,307,168.0 284.1 1,840.02,979.2 293 60.00 3.546 0.169 4.3 01/16/09 40,816,032.0 283.8 1,840.03,061.2 299 60.00 3.661 0.179 4.5 01/16/09 40,765,920.0 282.9 1,840.03,035.3 300 60.00 3.604 0.175 01/16/09 41,027,664.0 283.4 1,840.03,054.8 300 60.00 3.771 0.184

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 1.4 1.4 01/19/09 40,297,712.0 283.0 1,840.02,978.5 299 60.00 1.182 0.056 1.8 01/19/09 39,988,548.0 283.7 1,840.02,999.2 297 60.00 1.165 0.056 1.8 01/19/09 40,630,924.0 283.9 1,840.03,003.2 299 60.00 1.520 0.073 1.7 01/19/09 40,231,064.0 281.8 1,840.02,995.5 297 60.00 1.509 0.072 1.5 01/19/09 39,153,648.0 280.8 1,840.02,915.3 290 60.00 1.425 0.066 1.7 01/19/09 36,294,944.0 276.6 1,840.02,682.7 265 60.00 1.266 0.054 1.7 01/19/09 33,714,284.0 276.1 1,840.02,455.3 243 60.00 1.457 0.057 1.5 01/19/09 34,226,752.0 274.6 1,840.02,548.4 252 60.00 1.425 0.058 1.3 01/19/09 34,432,520.0 274.4 1,840.02,507.6 250 60.00 1.285 0.052 2.2 01/19/09 31,205,142.0 271.7 1,840.02,272.5 230 60.00 1.114 0.040 1.8 01/19/09 28,925,484.0 270.6 1,840.02,090.8 205 60.00 1.899 0.063 1.3 01/19/09 29,678,354.0 272.7 1,840.02,161.3 218 60.00 1.542 0.053 2.2 01/18/09 32,953,110.0 276.2 1,840.02,435.7 241 60.00 1.098 0.043 1.9 01/18/09 36,242,348.0 279.3 1,840.02,678.8 266 60.00 1.857 0.080 2.3 01/18/09 35,661,884.0 278.1 1,840.02,635.9 261 60.00 1.604 0.068 2.3 01/18/09 36,939,956.0 279.8 1,840.02,750.4 276 60.00 1.928 0.085 2.7 01/18/09 38,810,268.0 281.4 1,840.02,868.6 290 60.00 1.942 0.089 2.9 01/18/09 38,851,360.0 282.4 1,840.02,850.5 289 60.00 2.296 0.105 2.9 01/18/09 39,758,996.0 282.7 1,840.02,938.7 296 60.00 2.448 0.115 3.0 01/18/09 36,959,352.0 279.51,840.02,751.8 276 60.00 2.430 0.107 3.3 01/18/09 36,371,012.0 278.8 1,840.02,688.3 268 60.00 2.533 0.109 4.0 01/18/09 35,774,984.0 279.4 1,840.02,624.8 261 60.00 2.807 0.118 5.1 01/18/09 36,709,652.0 280.9 1,840.02,673.4 267 60.00 3.427 0.147 5.2 01/18/09 36,943,348.0 281.0 1,840.02,710.5 271 60.00 4.337 0.188 5.0 01/18/09 36,981,768.0 280.3 1,840.02,713.4 272 60.00 4.423 0.192 4.8 01/18/09 37,458,312.0 279.51,840.02,748.3 277 60.00 4.252 0.187 4.5 01/18/09 38,188,592.0 280.2 1,840.02,801.9 281 60.00 4.082 0.183 4.0 01/18/09 38,328,100.0 279.4 1,840.02,791.3 281 60.00 3.856 0.172 3.3 01/18/09 35,753,420.0 275.8 1,840.02,603.8 259 60.00 3.427 0.143 3.1 01/18/09 31,604,070.0 269.4 1,840.02,267.2 225 60.00 2.870 0.104 3.2 01/18/09 27,203,748.0 267.2 1,840.0 1,922.0 190 60.00 2.738 0.084 3.6 01/18/09 24,233,282.0 267.1 1,840.0 1,672.6 167 60.00 2.893 0.077 3.7 01/18/09 27,364,536.0 272.8 1,840.0 1,933.4 195 60.00 3.180 0.098 3.7 01/18/09 32,973,476.0 274.8 1,840.02,419.2 238 60.00 3.147 0.122 4.2 01/18/09 33,720,524.0 276.8 1,840.02,474.1 246 60.00 3.147 0.124 4.6 01/18/09 35,738,968.0 279.1 1,840.02,602.7 259 60.00 3.599 0.150 01/17/09 37,483,964.0 280.4 1,840.02,750.2 271 60.00 3.912 0.172

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 C 11:00 C 12:00 C 13:00 C 14:00 C 15:00 C 16:00 C 17:00 C 18:00 C 19:00 C 20:00 21:00 22:00 23:00 00:00 1.4 1.2 01/21/09 25,447,020.0 270.8 1,840.0 1,797.9 182 60.00 1.236 0.036 1.4 01/20/09 33,275,758.0 276.9 1,840.02,459.5 243 60.00 1.013 0.040 1.6 01/20/09 37,745,644.0 280.51,840.02,851.5 279 60.00 1.156 0.053 1.7 01/20/09 38,398,660.0 282.3 1,840.02,879.9 282 60.00 1.331 0.061 1.5 01/20/09 40,364,716.0 282.9 1,840.03,027.4 298 60.00 1.414 0.068 1.6 01/20/09 40,133,688.0 282.7 1,840.03,031.9 299 60.00 1.239 0.060 3.6 01/20/09 40,282,028.0 282.9 1,840.03,021.2 299 60.00 1.331 0.064 1.5 01/20/09 39,645,544.0 281.9 1,840.02,995.0 293 60.00 2.974 0.142 2.8 01/20/09 38,299,680.0 280.3 1,840.02,893.3 282 60.00 1.239 0.057 5.0 01/20/09 37,796,360.0 280.51,840.02,855.2 277 60.00 2.313 0.106 9.1 01/20/09 38,088,492.0 281.0 1,840.02,856.6 278 60.00 4.160 0.190 1.8 01/20/09 38,637,548.0 282.51,840.02,897.8 282 60.00 7.571 0.351 2.9 01/20/09 39,988,568.0 282.7 1,840.03,020.9 296 60.00 1.487 0.072 1.6 01/20/09 39,851,720.0 281.6 1,840.03,010.6 297 60.00 2.395 0.115 1.6 01/20/09 40,124,536.0 282.7 1,840.03,009.4 298 60.00 1.331 0.064 1.4 01/20/09 40,345,380.0 282.8 1,840.03,003.9 298 60.00 1.341 0.064 1.4 01/20/09 39,643,364.0 283.4 1,840.02,973.2 293 60.00 1.165 0.055 1.2 01/20/09 39,833,068.0 282.8 1,840.03,009.1 299 60.00 1.156 0.056 1.1 01/20/09 39,687,928.0 281.4 1,840.02,998.2 298 60.00 0.991 0.048 1.4 01/20/09 37,002,004.0 277.3 1,840.02,775.2 272 60.00 0.915 0.041 1.4 01/20/09 34,516,648.0 279.1 1,840.02,532.5 252 60.00 1.191 0.048 1.4 01/20/09 38,218,944.0 280.4 1,840.02,866.4 283 60.00 1.165 0.053 1.3 01/20/09 36,833,088.0 279.1 1,840.02,742.5 269 60.00 1.173 0.051 1.2 01/20/09 37,738,416.0 278.1 1,840.02,830.4 279 60.00 1.082 0.049 1.4 01/20/09 33,324,462.0 272.8 1,840.02,463.1 240 60.00 1.013 0.040 1.3 01/19/09 28,129,770.0 271.1 1,840.02,018.0 201 60.00 1.218 0.039 1.3 01/19/09 31,158,618.0 274.2 1,840.02,269.2 226 60.00 1.114 0.040 1.4 01/19/09 34,960,116.0 278.0 1,840.02,622.0 257 60.00 1.082 0.045 1.6 01/19/09 37,813,048.0 282.0 1,840.02,856.5 280 60.00 1.156 0.053 1.6 01/19/09 39,190,560.0 283.7 1,840.02,960.6 289 60.00 1.322 0.063 1.4 01/19/09 40,240,428.0 283.9 1,840.03,039.9 298 60.00 1.322 0.064 1.1 01/19/09 39,733,232.0 280.9 1,840.03,023.2 294 60.00 1.148 0.056 1.0 01/19/09 34,334,120.0 276.3 1,840.02,556.4 250 60.00 0.922 0.038 1.2 01/19/09 36,772,696.0 280.6 1,840.02,758.0 270 60.00 0.832 0.037 1.2 01/19/09 38,303,992.0 281.2 1,840.02,852.0 281 60.00 1.006 0.046 1.4 01/19/09 37,592,368.0 281.0 1,840.02,799.0 274 60.00 1.006 0.045 01/19/09 38,879,192.0 283.8 1,840.02,873.7 286 60.00 1.182 0.054

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 02:00 C C 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 C 10:00 C 11:00 C 12:00 C 13:00 C 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 2.7 3.5 01/22/09 35,151,292.0 279.8 1,840.02,540.8 248 60.00 2.331 0.095 4.1 01/22/09 36,639,564.0 283.1 1,840.02,668.3 261 60.00 2.999 0.128 4.3 01/22/09 39,885,320.0 284.51,840.02,926.3 291 60.00 3.487 0.163 4.1 01/22/09 40,794,952.0 286.3 1,840.02,993.1 297 60.00 3.657 0.175 2.8 01/22/09 41,198,512.0 285.6 1,840.03,000.4 300 60.00 3.513 0.169 3.0 01/22/09 41,209,972.0 284.8 1,840.03,001.2 299 60.00 2.399 0.115 3.2 01/22/09 40,866,144.0 284.51,840.02,998.3 299 60.00 2.551 0.122 2.5 01/22/09 39,838,744.0 283.9 1,840.02,901.3 289 60.00 2.742 0.127 2.3 01/22/09 37,778,900.0 278.7 1,840.02,751.3 268 60.00 2.142 0.094 2.0 01/22/09 31,407,854.0 272.3 1,840.02,253.2 223 60.00 2.001 0.072 1.9 01/22/09 28,474,596.0 269.7 1,840.0 1,996.3 197 60.00 1.780 0.057 2.0 01/22/09 26,687,582.0 269.4 1,840.0 1,813.0 183 60.00 1.745 0.051 2.3 01/22/09 27,153,674.0 270.51,840.0 1,874.2 187 60.00 1.808 0.054 2.1 01/22/09 27,088,368.0 268.7 1,840.0 1,899.1 189 60.00 2.047 0.062 2.3 01/21/09 25,917,754.0 270.1 1,840.0 1,788.9 183 60.00 1.899 0.054 3.0 01/21/09 31,903,976.0 276.9 1,840.02,271.4 229 60.00 2.016 0.073 3.0 01/21/09 35,983,476.0 280.6 1,840.02,581.4 256 60.00 2.609 0.108 2.7 01/21/09 38,616,920.0 283.2 1,840.02,791.3 279 60.00 2.590 0.116 2.3 01/21/09 40,706,520.0 283.2 1,840.02,986.7 298 60.00 2.296 0.110 1.4 01/21/09 39,447,964.0 281.51,840.02,915.7 290 60.00 1.942 0.091 0.4 01/21/09 37,118,056.0 278.1 1,840.02,723.3 268 60.00 1.191 0.052 0.9 01/21/09 32,443,486.0 273.51,840.02,362.7 226 60.00 0.343 0.013 2.5 01/21/09 29,571,236.0 270.4 1,840.02,073.2 203 60.00 0.801 0.027 2.4 01/21/09 28,572,520.0 270.6 1,840.02,018.7 202 60.00 2.208 0.071 2.2 01/21/09 29,965,508.0 270.9 1,840.02,149.7 210 60.00 2.088 0.072 4.1 01/21/09 28,339,236.0 269.2 1,840.0 1,986.8 193 60.00 1.958 0.062 2.4 01/21/09 27,879,564.0 269.6 1,840.0 1,939.5 190 60.00 3.678 0.114 2.0 01/21/09 28,348,142.0 270.3 1,840.02,002.8 196 60.00 2.120 0.068 2.1 01/21/09 28,476,446.0 270.4 1,840.02,027.4 198 60.00 1.753 0.057 2.0 01/21/09 30,335,806.0 276.1 1,840.02,176.3 221 60.00 1.827 0.064 1.8 01/21/09 37,048,704.0 274.7 1,840.02,657.9 270 60.00 1.740 0.074 1.7 01/21/09 30,159,110.0 268.4 1,840.02,114.4 211 60.00 1.602 0.054 1.7 01/21/09 27,140,196.0 267.0 1,840.0 1,888.0 189 60.00 1.525 0.046 3.9 01/21/09 26,149,028.0 265.1 1,840.0 1,790.6 181 60.00 1.549 0.044 1.3 01/21/09 25,172,520.0 265.1 1,840.0 1,764.8 179 60.00 3.471 0.098 1.3 01/21/09 25,471,692.0 265.1 1,840.0 1,772.0 179 60.00 1.166 0.033 01/21/09 23,758,302.0 266.1 1,840.0 1,601.1 161 60.00 1.204 0.031

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 C 02:00 C C 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 2.4 2.5 01/24/09 28,426,942.0 271.3 1,840.02,039.3 195 60.00 2.088 0.068 2.5 01/24/09 27,749,120.0 270.7 1,840.02,005.8 189 60.00 2.158 0.069 2.6 01/24/09 27,144,502.0 269.8 1,840.0 1,976.9 191 60.00 2.142 0.068 3.6 01/23/09 31,295,196.0 275.8 1,840.02,245.1 227 60.00 2.262 0.081 3.5 01/23/09 36,106,220.0 279.3 1,840.02,629.5 257 60.00 3.085 0.130 3.2 01/23/09 35,691,296.0 278.0 1,840.02,599.2 251 60.00 2.999 0.125 3.3 01/23/09 35,611,280.0 279.6 1,840.02,574.1 255 60.00 2.762 0.114 3.1 01/23/09 38,803,592.0 282.3 1,840.02,847.0 283 60.00 2.807 0.128 2.7 01/23/09 40,000,980.0 283.1 1,840.02,956.6 292 60.00 2.617 0.124 2.3 01/23/09 40,187,908.0 282.6 1,840.02,970.4 292 60.00 2.279 0.108 2.2 01/23/09 37,526,524.0 280.0 1,840.02,753.3 268 60.00 1.956 0.086 1.9 01/23/09 36,348,304.0 278.9 1,840.02,647.1 256 60.00 1.885 0.080 1.8 01/23/09 34,688,384.0 275.6 1,840.02,507.3 245 60.00 1.640 0.066 1.4 01/23/09 34,027,220.0 277.1 1,840.02,441.1 243 60.00 1.566 0.061 1.6 01/23/09 36,053,736.0 279.1 1,840.02,606.1 257 60.00 1.209 0.050 2.5 01/23/09 38,562,476.0 282.0 1,840.02,808.3 278 60.00 1.371 0.062 3.2 01/23/09 37,646,252.0 282.51,840.02,741.6 270 60.00 2.142 0.094 3.4 01/23/09 37,918,720.0 281.3 1,840.02,761.5 274 60.00 2.742 0.121 3.3 01/23/09 38,799,472.0 282.9 1,840.02,825.6 283 60.00 2.913 0.132 2.3 01/23/09 39,644,480.0 282.0 1,840.02,865.6 290 60.00 2.849 0.131 2.2 01/23/09 36,208,412.0 276.9 1,840.02,617.2 259 60.00 1.986 0.083 2.0 01/23/09 31,609,168.0 271.1 1,840.02,284.8 221 60.00 1.899 0.069 1.8 01/23/09 27,097,050.0 268.9 1,840.0 1,899.7 186 60.00 1.780 0.054 5.9 01/23/09 26,201,994.0 268.3 1,840.0 1,808.5 177 60.00 1.627 0.047 1.9 01/23/09 26,485,580.0 267.7 1,840.0 1,813.7 180 60.00 5.376 0.156 2.0 01/23/09 26,051,558.0 268.7 1,840.0 1,784.0 178 60.00 1.731 0.049 1.3 01/23/09 27,295,958.0 268.9 1,840.0 1,869.2 185 60.00 1.822 0.054 2.5 01/22/09 26,372,844.0 270.0 1,840.0 1,806.0 181 60.00 1.185 0.034 3.8 01/22/09 29,548,702.0 274.3 1,840.02,039.5 207 60.00 2.260 0.074 4.3 01/22/09 35,024,676.0 282.2 1,840.02,512.7 249 60.00 3.305 0.133 4.4 01/22/09 40,678,828.0 285.7 1,840.02,918.3 289 60.00 3.740 0.175 3.9 01/22/09 40,736,664.0 285.4 1,840.02,944.6 294 60.00 3.798 0.179 3.8 01/22/09 40,973,272.0 286.0 1,840.02,983.9 298 60.00 3.342 0.159 3.4 01/22/09 41,137,024.0 285.1 1,840.02,995.8 298 60.00 3.256 0.156 2.8 01/22/09 36,705,648.0 277.8 1,840.02,693.1 263 60.00 2.892 0.125 2.5 01/22/09 34,443,476.0 278.3 1,840.02,470.9 247 60.00 2.435 0.096 01/22/09 36,280,344.0 279.51,840.02,642.1 257 60.00 2.142 0.091

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 3.1 2.4 01/25/09 38,597,412.0 284.2 1,840.02,915.8 283 60.00 2.561 0.119 2.1 01/25/09 39,559,244.0 284.1 1,840.02,966.9 289 60.00 1.997 0.095 1.8 01/25/09 39,344,796.0 283.8 1,840.02,929.5 288 60.00 1.760 0.082 2.2 01/25/09 39,357,592.0 282.7 1,840.02,909.1 288 60.00 1.520 0.071 3.1 01/25/09 39,303,312.0 284.8 1,840.02,905.0 292 60.00 1.857 0.086 2.7 01/25/09 40,940,520.0 286.3 1,840.03,048.3 300 60.00 2.598 0.127 2.1 01/25/09 39,640,120.0 283.3 1,840.03,037.6 295 60.00 2.199 0.107 2.4 01/25/09 38,978,928.0 283.9 1,840.02,987.0 290 60.00 1.710 0.082 1.8 01/25/09 39,394,928.0 282.6 1,840.02,997.4 292 60.00 1.968 0.094 1.4 01/25/09 37,484,576.0 280.51,840.02,831.7 275 60.00 1.487 0.067 1.5 01/25/09 34,624,620.0 275.3 1,840.02,578.1 252 60.00 1.173 0.048 1.8 01/25/09 33,404,736.0 276.6 1,840.02,469.1 246 60.00 1.266 0.050 2.3 01/25/09 34,248,260.0 280.2 1,840.02,531.4 252 60.00 1.520 0.062 2.3 01/25/09 38,667,244.0 284.2 1,840.02,858.0 286 60.00 1.942 0.089 1.6 01/25/09 38,052,204.0 282.3 1,840.02,895.3 279 60.00 1.886 0.087 1.3 01/25/09 36,492,584.0 281.8 1,840.02,756.8 270 60.00 1.322 0.058 2.6 01/24/09 37,932,964.0 280.9 1,840.02,906.8 280 60.00 1.059 0.049 2.9 01/24/09 35,274,632.0 280.1 1,840.02,664.8 258 60.00 2.148 0.092 3.4 01/24/09 36,578,084.0 279.7 1,840.02,743.4 269 60.00 2.413 0.106 3.6 01/24/09 38,613,348.0 284.1 1,840.02,917.0 285 60.00 2.808 0.131 3.7 01/24/09 39,562,128.0 284.3 1,840.02,988.7 292 60.00 2.974 0.142 3.1 01/24/09 40,297,060.0 284.0 1,840.03,044.2 297 60.00 3.056 0.149 2.1 01/24/09 38,463,592.0 278.3 1,840.02,905.7 283 60.00 2.561 0.119 2.1 01/24/09 33,797,588.0 274.9 1,840.02,461.4 244 60.00 1.799 0.071 1.7 01/24/09 32,674,614.0 275.2 1,840.02,432.9 233 60.00 1.760 0.068 2.3 01/24/09 31,279,342.0 274.2 1,840.02,294.9 222 60.00 1.446 0.053 3.0 01/24/09 33,480,410.0 276.0 1,840.02,474.6 241 60.00 1.942 0.077 3.6 01/24/09 35,880,448.0 280.3 1,840.02,652.0 260 60.00 2.533 0.107 4.1 01/24/09 37,187,404.0 281.8 1,840.02,748.6 272 60.00 3.039 0.134 4.1 01/24/09 39,249,288.0 283.7 1,840.02,943.7 290 60.00 3.411 0.161 3.5 01/24/09 39,369,644.0 282.1 1,840.02,952.8 292 60.00 3.411 0.161 2.7 01/24/09 38,695,052.0 280.2 1,840.02,902.1 287 60.00 2.912 0.135 2.6 01/24/09 35,806,308.0 277.4 1,840.02,646.5 260 60.00 2.279 0.096 1.9 01/24/09 34,856,304.0 276.8 1,840.02,538.4 249 60.00 2.228 0.090 2.6 01/24/09 33,912,268.0 274.2 1,840.02,414.4 240 60.00 1.665 0.064 2.4 01/24/09 32,912,206.0 272.4 1,840.02,361.1 231 60.00 2.262 0.085 01/24/09 29,015,452.0 271.6 1,840.02,097.3 205 60.00 2.072 0.069

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 1.4 1.7 01/27/09 31,492,730.3 274.8 1,840.02,327.7 226 60.00 1.182 0.044 1.5 01/27/09 34,240,559.0 276.2 1,840.02,530.9 247 60.00 1.435 0.058 1.8 01/27/09 32,465,727.7 276.1 1,840.02,364.4 234 60.00 1.285 0.049 1.9 01/27/09 33,354,775.9 279.51,840.02,465.4 240 60.00 1.520 0.060 1.6 01/27/09 37,267,201.2 281.2 1,840.02,835.5 271 60.00 1.558 0.071 2.8 01/26/09 36,188,840.8 281.1 1,840.02,714.2 265 60.00 1.331 0.058 3.0 01/26/09 40,132,151.3 285.6 1,840.03,009.9 295 60.00 2.330 0.112 3.0 01/26/09 40,305,642.8 287.1 1,840.03,023.0 294 60.00 2.496 0.121 3.4 01/26/09 41,043,542.6 287.3 1,840.03,078.3 300 60.00 2.496 0.123 3.4 01/26/09 40,561,666.1 286.8 1,840.03,064.2 299 60.00 2.808 0.138 2.6 01/26/09 40,876,925.6 286.51,840.03,088.0 300 60.00 2.808 0.139 2.5 01/26/09 40,898,131.7 286.8 1,840.03,089.6 300 60.00 2.148 0.106 2.9 01/26/09 40,672,273.4 287.1 1,840.03,050.4 296 60.00 2.080 0.101 2.9 01/26/09 41,362,855.9 287.8 1,840.03,079.7 299 60.00 2.430 0.120 2.7 01/26/09 40,694,289.4 286.2 1,840.03,074.2 297 60.00 2.395 0.118 2.6 01/26/09 40,228,149.8 286.1 1,840.03,017.1 294 60.00 2.246 0.108 3.2 01/26/09 41,169,299.3 287.9 1,840.03,110.0 300 60.00 2.148 0.107 3.4 01/26/09 41,235,963.8 287.3 1,840.03,092.7 299 60.00 2.662 0.132 3.4 01/26/09 41,010,195.6 286.4 1,840.03,031.2 299 60.00 2.870 0.139 2.9 01/26/09 40,634,264.0 285.1 1,840.03,003.4 298 60.00 2.870 0.138 2.6 01/26/09 40,491,924.0 284.3 1,840.02,992.9 298 60.00 2.448 0.117 2.0 01/26/09 40,363,008.0 283.3 1,840.03,005.3 298 60.00 2.179 0.105 1.4 01/26/09 40,584,136.0 284.1 1,840.03,021.7 298 60.00 1.676 0.081 0.8 01/26/09 38,499,332.0 279.9 1,840.02,866.5 279 60.00 1.173 0.054 1.0 01/26/09 35,325,000.0 276.51,840.02,591.8 250 60.00 0.680 0.028 1.0 01/26/09 31,983,852.0 277.9 1,840.02,364.0 232 60.00 0.844 0.032 1.1 01/26/09 33,504,272.0 276.51,840.02,440.0 243 60.00 0.857 0.033 1.3 01/26/09 30,560,176.0 273.6 1,840.02,192.3 217 60.00 0.957 0.034 1.5 01/26/09 29,268,958.0 275.3 1,840.02,115.6 213 60.00 1.122 0.038 1.7 01/25/09 35,322,900.0 281.7 1,840.02,610.8 261 60.00 1.266 0.053 2.5 01/25/09 39,611,228.0 286.1 1,840.02,992.4 295 60.00 1.404 0.067 2.7 01/25/09 39,976,504.0 287.8 1,840.02,998.3 296 60.00 2.080 0.100 3.6 01/25/09 40,831,044.0 288.51,840.03,040.1 300 60.00 2.263 0.110 3.5 01/25/09 40,851,544.0 287.6 1,840.03,019.5 299 60.00 3.039 0.147 3.7 01/25/09 40,721,392.0 287.3 1,840.03,009.8 299 60.00 2.955 0.142 3.4 01/25/09 40,680,512.0 286.9 1,840.03,051.1 299 60.00 3.078 0.150 01/25/09 37,765,940.0 283.1 1,840.02,853.0 274 60.00 2.808 0.128

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 S S S 10:00 11:00 12:00 C 13:00 C 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 2.9 2.6 01/28/09 41,073,046.3 284.3 1,840.02,968.9 299 60.00 2.504 0.119 2.0 01/28/09 39,804,051.0 282.7 1,840.02,898.8 286 60.00 2.228 0.103 1.7 01/28/09 36,269,133.1 277.9 1,840.02,601.9 255 60.00 1.740 0.072 1.7 01/28/09 34,020,172.2 276.6 1,840.02,440.6 241 60.00 1.479 0.058 1.8 01/28/09 36,522,298.7 281.0 1,840.02,659.8 263 60.00 1.457 0.062 2.8 01/28/09 37,443,494.6 281.0 1,840.02,706.5 269 60.00 1.554 0.067 2.8 01/28/09 37,192,611.5 283.3 1,840.02,688.4 266 60.00 2.417 0.104 2.5 01/28/09 39,945,714.0 283.7 1,840.02,909.1 293 60.00 2.399 0.112 2.4 01/28/09 40,229,139.1 283.2 1,840.02,929.7 296 60.00 2.142 0.100 2.4 01/28/09 40,865,520.3 284.8 1,840.02,976.1 300 60.00 2.056 0.098 2.1 01/28/09 41,181,666.8 284.4 1,840.02,976.7 299 60.00 2.072 0.099 1.6 01/28/09 39,243,619.7 279.8 1,840.02,836.7 281 60.00 1.813 0.082 1.5 01/28/09 34,497,805.7 273.7 1,840.02,493.6 245 60.00 1.381 0.055 1.2 01/28/09 30,109,938.3 271.9 1,840.02,160.1 211 60.00 1.305 0.045 1.0 01/28/09 30,588,934.5 272.4 1,840.02,161.2 213 60.00 1.060 0.037 1.5 01/28/09 30,200,442.2 272.2 1,840.02,100.9 208 60.00 0.897 0.030 1.6 01/28/09 30,258,823.8 272.7 1,840.02,187.2 214 60.00 1.295 0.045 1.3 01/28/09 32,053,283.6 274.3 1,840.02,334.3 229 60.00 1.371 0.051 2.2 01/27/09 30,480,928.8 276.2 1,840.02,203.2 216 60.00 1.122 0.040 1.9 01/27/09 37,672,975.2 281.6 1,840.02,723.1 272 60.00 1.899 0.083 2.5 01/27/09 36,689,054.9 279.1 1,840.02,671.9 262 60.00 1.628 0.070 2.9 01/27/09 35,956,785.2 281.9 1,840.02,657.7 262 60.00 2.111 0.090 3.2 01/27/09 40,765,015.0 285.1 1,840.02,990.9 299 60.00 2.466 0.118 3.4 01/27/09 40,964,436.0 286.2 1,840.03,005.5 299 60.00 2.722 0.131 3.6 01/27/09 40,946,381.5 286.1 1,840.03,004.2 299 60.00 2.892 0.139 3.5 01/27/09 40,048,374.4 284.7 1,840.02,981.8 295 60.00 3.017 0.144 2.9 01/27/09 40,427,629.0 285.0 1,840.03,032.1 299 60.00 2.912 0.141 2.8 01/27/09 40,651,635.8 285.2 1,840.03,048.9 299 60.00 2.413 0.118 9.8 01/27/09 40,877,008.3 285.7 1,840.03,043.6 300 60.00 2.347 0.114 1.6 01/27/09 40,999,655.6 286.1 1,840.03,052.7 299 60.00 8.213 0.401 2.5 01/27/09 40,722,950.5 286.1 1,840.03,032.1 300 60.00 1.341 0.065 12.5 01/27/09 41,085,233.7 286.51,840.03,059.0 300 60.00 2.095 0.102 2.5 01/27/09 40,422,222.7 284.51,840.03,053.6 299 60.00 10.325 0.504 2.4 01/27/09 40,915,415.6 286.6 1,840.03,090.9 300 60.00 2.065 0.102 1.6 01/27/09 41,011,020.0 285.3 1,840.03,098.1 297 60.00 1.982 0.098 1.4 01/27/09 39,391,639.3 280.4 1,840.02,911.6 284 60.00 1.351 0.063 01/27/09 34,872,217.9 276.4 1,840.02,596.4 251 60.00 1.173 0.049

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 S S S 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 C 02:00 C C 03:00 C 04:00 C 05:00 C C 06:00 1.8 0.9 01/30/09 39,115,748.0 277.9 1,840.02,848.7 283 60.00 1.542 0.070 1.4 01/30/09 32,673,528.3 272.9 1,840.02,308.5 229 60.00 0.795 0.029 1.2 01/30/09 32,153,776.9 273.8 1,840.02,254.3 225 60.00 1.246 0.045 5.9 01/30/09 30,938,151.1 271.7 1,840.02,152.2 211 60.00 1.076 0.037 1.2 01/30/09 29,497,343.2 272.2 1,840.02,019.9 207 60.00 5.376 0.174 1.0 01/30/09 32,188,278.7 274.6 1,840.02,274.2 226 60.00 1.060 0.039 1.6 01/30/09 33,586,484.3 276.2 1,840.02,391.2 234 60.00 0.876 0.034 2.4 01/29/09 34,388,209.8 280.0 1,840.02,504.3 242 60.00 1.371 0.055 3.3 01/29/09 35,884,933.0 280.6 1,840.02,632.9 257 60.00 2.041 0.086 3.2 01/29/09 38,824,341.8 284.3 1,840.02,848.5 279 60.00 2.807 0.128 3.5 01/29/09 40,260,407.0 286.3 1,840.02,932.0 290 60.00 2.742 0.129 3.5 01/29/09 41,175,246.9 286.4 1,840.02,998.6 298 60.00 2.999 0.144 3.5 01/29/09 40,788,877.9 285.51,840.02,970.5 298 60.00 2.999 0.142 3.4 01/29/09 40,949,854.3 286.0 1,840.02,982.2 297 60.00 2.999 0.143 3.4 01/29/09 39,569,382.4 285.1 1,840.02,881.7 285 60.00 2.913 0.134 3.7 01/29/09 39,827,438.3 285.3 1,840.02,900.4 287 60.00 2.913 0.135 3.2 01/29/09 40,577,998.4 286.3 1,840.02,955.1 296 60.00 3.170 0.150 3.2 01/29/09 40,369,938.3 286.1 1,840.02,961.9 294 60.00 2.722 0.129 2.9 01/29/09 40,890,880.1 285.2 1,840.02,977.9 298 60.00 2.742 0.131 2.8 01/29/09 40,906,228.3 285.8 1,840.02,979.0 298 60.00 2.485 0.118 12.5 01/29/09 41,304,445.8 286.1 1,840.02,985.6 300 60.00 2.417 0.115 2.6 01/29/09 41,093,672.0 285.8 1,840.02,970.4 298 60.00 10.791 0.513 2.2 01/29/09 40,642,894.3 284.0 1,840.02,959.9 297 60.00 2.228 0.105 1.6 01/29/09 41,006,857.7 284.4 1,840.02,964.1 297 60.00 1.899 0.090 1.1 01/29/09 36,910,842.9 276.1 1,840.02,607.8 255 60.00 1.413 0.059 1.1 01/29/09 28,598,417.9 270.2 1,840.0 1,958.3 193 60.00 1.002 0.031 1.0 01/29/09 27,268,349.0 268.4 1,840.0 1,882.1 188 60.00 0.994 0.030 0.9 01/29/09 26,340,887.3 268.4 1,840.0 1,803.8 181 60.00 0.911 0.026 0.8 01/29/09 26,802,852.7 269.1 1,840.0 1,806.3 184 60.00 0.833 0.024 1.6 01/29/09 26,455,634.6 269.7 1,840.0 1,797.3 179 60.00 0.735 0.021 1.5 01/29/09 27,739,615.6 271.2 1,840.0 1,929.7 191 60.00 1.435 0.044 2.2 01/28/09 30,487,286.0 275.0 1,840.02,154.0 218 60.00 1.325 0.046 2.3 01/28/09 34,712,554.2 279.4 1,840.02,528.0 248 60.00 1.885 0.076 2.8 01/28/09 36,648,542.7 284.3 1,840.02,649.1 262 60.00 1.986 0.084 3.5 01/28/09 40,178,336.7 286.0 1,840.02,904.2 290 60.00 2.417 0.112 3.3 01/28/09 40,915,654.1 286.7 1,840.02,979.8 298 60.00 2.999 0.143 01/28/09 41,041,996.3 285.3 1,840.02,988.9 299 60.00 2.828 0.135

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 2.6 1.9 01/31/09 38,108,208.4 282.8 1,840.02,754.5 274 60.00 2.245 0.099 1.1 01/31/09 38,647,006.4 283.0 1,840.02,793.5 279 60.00 1.640 0.073 0.7 01/31/09 35,426,912.1 273.9 1,840.02,522.2 244 60.00 0.964 0.039 0.7 01/31/09 28,140,376.0 268.51,840.0 1,896.4 189 60.00 0.648 0.020 0.6 01/31/09 26,797,433.7 266.6 1,840.0 1,805.9 181 60.00 0.648 0.019 0.5 01/31/09 26,184,186.4 266.8 1,840.0 1,764.6 179 60.00 0.556 0.016 0.7 01/31/09 28,152,636.6 270.2 1,840.0 1,927.9 194 60.00 0.456 0.014 1.4 01/31/09 29,619,974.3 272.7 1,840.02,028.3 205 60.00 0.638 0.021 1.7 01/31/09 33,119,987.7 275.1 1,840.02,268.0 231 60.00 1.276 0.046 1.2 01/31/09 34,460,162.3 276.2 1,840.02,397.2 241 60.00 1.525 0.058 1.3 01/31/09 34,788,915.9 275.9 1,840.02,420.1 242 60.00 1.076 0.042 1.4 01/31/09 33,397,751.7 275.3 1,840.02,395.9 235 60.00 1.131 0.043 1.3 01/31/09 35,882,354.5 279.1 1,840.02,652.1 256 60.00 1.182 0.050 0.9 01/31/09 35,681,871.4 274.8 1,840.02,540.4 243 60.00 1.139 0.046 0.9 01/31/09 30,079,117.4 270.6 1,840.02,108.8 204 60.00 0.801 0.027 1.0 01/31/09 27,815,916.9 267.8 1,840.0 1,935.0 189 60.00 0.807 0.025 1.1 01/31/09 26,661,416.7 267.7 1,840.0 1,854.7 182 60.00 0.897 0.027 2.1 01/31/09 27,906,772.9 272.6 1,840.0 1,941.4 193 60.00 0.987 0.031 1.3 01/31/09 34,003,187.2 277.8 1,840.02,457.8 240 60.00 1.813 0.071 1.3 01/31/09 35,898,571.2 278.1 1,840.02,614.4 251 60.00 1.114 0.047 2.8 01/30/09 33,899,333.1 278.4 1,840.02,487.2 239 60.00 1.106 0.044 3.0 01/30/09 37,524,515.2 282.0 1,840.02,773.6 272 60.00 2.364 0.105 3.4 01/30/09 39,365,721.2 283.3 1,840.02,909.7 285 60.00 2.533 0.118 3.3 01/30/09 40,253,800.7 285.3 1,840.02,975.3 291 60.00 2.870 0.137 3.3 01/30/09 41,193,300.5 285.8 1,840.03,044.7 298 60.00 2.786 0.136 3.3 01/30/09 40,745,687.7 286.3 1,840.03,011.7 296 60.00 2.786 0.134 2.6 01/30/09 39,888,696.4 283.2 1,840.02,970.0 291 60.00 2.766 0.131 2.4 01/30/09 36,583,344.6 279.8 1,840.02,704.0 263 60.00 2.195 0.095 3.7 01/30/09 35,971,539.7 279.7 1,840.02,678.3 259 60.00 2.011 0.086 3.6 01/30/09 37,485,587.2 282.2 1,840.02,770.7 273 60.00 3.124 0.138 3.8 01/30/09 40,232,018.6 285.1 1,840.02,973.7 292 60.00 3.039 0.145 3.5 01/30/09 40,996,782.6 286.0 1,840.03,007.9 297 60.00 3.232 0.155 3.5 01/30/09 41,252,528.3 286.0 1,840.03,004.3 299 60.00 2.999 0.144 3.1 01/30/09 40,816,469.6 285.9 1,840.03,016.8 299 60.00 2.955 0.143 2.7 01/30/09 40,712,749.1 285.2 1,840.03,009.2 300 60.00 2.617 0.126 2.3 01/30/09 40,599,206.9 284.4 1,840.03,000.8 299 60.00 2.279 0.109 01/30/09 40,346,450.4 282.8 1,840.02,982.1 296 60.00 1.942 0.093

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 3.4 3.4 02/02/09 38,449,422.2 286.2 1,840.02,821.0 278 60.00 2.892 0.130 2.7 02/02/09 39,681,184.9 285.2 1,840.02,932.9 288 60.00 2.870 0.135 2.0 02/02/09 35,261,481.5 277.4 1,840.02,567.9 252 60.00 2.313 0.095 1.6 02/02/09 30,080,339.0 272.2 1,840.02,141.6 208 60.00 1.753 0.060 1.4 02/02/09 26,339,571.2 270.3 1,840.0 1,818.0 181 60.00 1.447 0.042 1.6 02/02/09 26,559,480.3 269.8 1,840.0 1,833.1 182 60.00 1.266 0.037 1.7 02/02/09 26,342,674.1 270.6 1,840.0 1,789.6 182 60.00 1.470 0.042 1.8 02/02/09 27,230,630.5 270.8 1,840.0 1,864.7 187 60.00 1.549 0.046 1.3 02/02/09 26,964,506.6 269.6 1,840.0 1,861.2 187 60.00 1.627 0.048 1.8 02/01/09 26,207,230.8 270.2 1,840.0 1,808.9 183 60.00 1.175 0.034 1.9 02/01/09 27,370,008.6 273.4 1,840.0 1,889.1 193 60.00 1.627 0.049 2.1 02/01/09 28,939,875.5 272.4 1,840.02,013.2 201 60.00 1.704 0.055 1.8 02/01/09 29,604,468.1 275.0 1,840.02,075.5 210 60.00 1.869 0.062 2.2 02/01/09 28,775,621.9 272.51,840.02,017.4 199 60.00 1.602 0.052 2.3 02/01/09 29,011,315.0 276.3 1,840.02,018.2 203 60.00 1.973 0.064 1.6 02/01/09 33,601,174.8 277.9 1,840.02,447.0 233 60.00 1.971 0.077 1.5 02/01/09 28,014,380.6 273.0 1,840.0 1,964.0 193 60.00 1.424 0.045 1.3 02/01/09 27,786,831.4 272.0 1,840.0 1,917.9 188 60.00 1.356 0.042 1.0 02/01/09 26,833,059.3 270.1 1,840.0 1,852.1 184 60.00 1.175 0.035 1.1 02/01/09 26,267,308.6 269.3 1,840.0 1,813.0 181 60.00 0.904 0.026 1.7 02/01/09 26,662,913.6 269.8 1,840.0 1,854.8 185 60.00 0.987 0.029 1.4 02/01/09 26,469,124.5 271.51,840.0 1,870.1 184 60.00 1.501 0.045 1.1 02/01/09 26,741,196.8 271.51,840.0 1,889.3 183 60.00 1.236 0.037 1.2 02/01/09 26,782,288.3 271.1 1,840.0 1,892.2 181 60.00 0.972 0.029 1.1 02/01/09 25,785,419.0 269.6 1,840.0 1,835.8 180 60.00 1.052 0.031 1.2 02/01/09 25,753,068.9 268.6 1,840.0 1,791.5 180 60.00 0.987 0.028 1.1 02/01/09 26,105,949.3 270.8 1,840.0 1,830.3 184 60.00 1.068 0.031 0.9 02/01/09 26,766,561.2 270.4 1,840.0 1,862.1 183 60.00 0.987 0.029 0.9 02/01/09 27,374,683.4 270.1 1,840.0 1,904.3 186 60.00 0.807 0.025 0.8 02/01/09 25,558,973.5 269.51,840.0 1,778.0 177 60.00 0.807 0.023 1.0 02/01/09 26,367,931.7 270.51,840.0 1,805.6 182 60.00 0.729 0.021 1.2 02/01/09 27,004,922.2 272.0 1,840.0 1,893.3 187 60.00 0.890 0.027 1.0 02/01/09 26,887,269.0 269.3 1,840.0 1,885.0 185 60.00 1.068 0.032 0.9 01/31/09 25,629,092.4 269.1 1,840.0 1,769.0 178 60.00 0.904 0.026 1.2 01/31/09 26,937,036.1 270.2 1,840.0 1,844.6 184 60.00 0.820 0.024 2.1 01/31/09 27,897,668.1 274.6 1,840.0 1,910.4 194 60.00 1.093 0.033 01/31/09 34,706,401.0 281.0 1,840.02,470.9 246 60.00 1.841 0.073

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 10:00 11:00 12:00 13:00 S IM S S S 14:00 15:00 16:00 17:00 18:00 C 19:00 C 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 S S 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 4.9 4.7 02/03/09 41,500,756.7 286.7 1,840.03,044.9 299 60.00 4.167 0.203 4.7 02/03/09 41,578,799.3 287.1 1,840.03,050.6 300 60.00 3.997 0.195 4.5 02/03/09 41,523,540.4 287.0 1,840.03,046.6 300 60.00 3.997 0.195 4.1 02/03/09 41,564,595.8 285.51,840.03,049.6 301 60.00 3.827 0.187 4.0 02/03/09 41,475,402.2 286.0 1,840.02,997.9 300 60.00 3.539 0.170 3.2 02/03/09 40,757,405.3 285.8 1,840.02,968.2 294 60.00 3.427 0.163 3.1 02/03/09 39,919,056.2 283.7 1,840.02,907.1 286 60.00 2.742 0.127 3.6 02/03/09 37,540,299.0 284.6 1,840.02,733.9 269 60.00 2.656 0.116 3.6 02/03/09 40,254,592.2 286.8 1,840.02,931.6 292 60.00 3.085 0.145 3.3 02/03/09 41,296,241.5 286.9 1,840.02,985.0 299 60.00 3.108 0.148 3.6 02/03/09 41,025,655.1 286.8 1,840.02,987.8 299 60.00 2.828 0.135 3.7 02/03/09 41,228,470.3 287.1 1,840.02,980.1 299 60.00 3.108 0.148 3.7 02/03/09 41,382,256.1 287.6 1,840.02,991.2 299 60.00 3.194 0.153 3.6 02/03/09 41,128,396.6 288.1 1,840.02,995.2 299 60.00 3.170 0.152 3.2 02/03/09 41,080,782.1 287.1 1,840.02,991.8 300 60.00 3.085 0.148 2.5 02/03/09 40,844,546.6 285.2 1,840.02,996.8 296 60.00 2.722 0.130 1.5 02/03/09 35,629,166.5 278.9 1,840.02,575.4 252 60.00 2.158 0.089 1.3 02/03/09 32,328,084.5 275.6 1,840.02,336.8 227 60.00 1.295 0.048 1.3 02/03/09 28,105,415.8 270.51,840.02,001.0 199 60.00 1.139 0.036 1.6 02/03/09 26,609,810.8 270.3 1,840.0 1,865.6 186 60.00 1.157 0.035 2.0 02/03/09 26,298,356.7 270.6 1,840.0 1,843.7 184 60.00 1.424 0.042 2.3 02/03/09 27,244,304.1 270.7 1,840.0 1,880.4 186 60.00 1.808 0.054 2.9 02/02/09 27,148,337.5 274.0 1,840.0 1,873.8 191 60.00 2.079 0.062 3.3 02/02/09 33,734,656.4 278.9 1,840.02,420.1 237 60.00 2.522 0.098 4.0 02/02/09 34,673,546.5 281.51,840.02,487.5 244 60.00 2.870 0.114 4.0 02/02/09 38,712,371.0 286.8 1,840.02,840.3 278 60.00 3.402 0.155 3.8 02/02/09 41,295,383.7 289.3 1,840.03,029.8 298 60.00 3.402 0.165 3.3 02/02/09 41,535,745.9 289.0 1,840.03,024.9 300 60.00 3.256 0.157 2.5 02/02/09 40,576,272.0 284.3 1,840.02,955.0 290 60.00 2.828 0.134 2.2 02/02/09 32,397,553.4 273.2 1,840.02,324.2 224 60.00 2.175 0.081 2.2 02/02/09 28,785,945.1 271.8 1,840.02,049.4 200 60.00 1.928 0.063 2.9 02/02/09 29,728,734.6 276.2 1,840.02,100.4 209 60.00 1.943 0.065 3.2 02/02/09 35,602,000.0 139.2 1,840.02,554.1 238 60.00 2.522 0.103 3.1 02/02/09 37,108,447.1 280.8 1,840.02,682.3 262 60.00 2.762 0.118 2.6 02/02/09 34,112,179.4 279.1 1,840.02,465.7 242 60.00 2.676 0.106 3.3 02/02/09 34,722,321.9 280.4 1,840.02,490.9 242 60.00 2.262 0.090 02/02/09 36,320,652.4 283.9 1,840.02,625.4 259 60.00 2.849 0.120

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F FC 16:00 F F F F F F F F FC 17:00 F F F F F F F F FC 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 0.0 0.0 02/05/09 3,687,323.6 80.6 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,705,535.4 82.51,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,820,026.5 84.51,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,906,044.2 86.4 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,889,001.8 88.51,840.0 0.0 0 0.00 0.000 2.4 02/05/09 3,837,673.7 90.9 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,848,179.9 93.51,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,822,209.3 96.6 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 9,384,085.8 100.3 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,821,485.4 104.2 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,869,927.4 108.9 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 3,822,328.6 114.1 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 3,802,951.8 120.3 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 11,312,404.0 129.9 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 11,590,714.7 140.1 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 11,557,279.1 149.4 1,840.0 0.0 0 0.00 0.000 0.9 02/04/09 11,513,567.4 155.8 1,840.0 0.0 0 0.00 0.000 5.5 02/04/09 11,335,787.9 160.7 1,840.0 0.0 0 0.00 0.000 0.3 02/04/09 11,111,581.7 166.6 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 11,279,640.3 170.3 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 11,495,928.8 169.9 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 11,598,445.2 166.1 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 12,420,240.6 168.6 1,840.0 0.0 0 0.00 0.000 0.0 02/04/09 10,895,181.7 164.0 1,840.0 0.0 0 0.00 0.000 0.4 02/04/09 12,896,195.8 163.1 1,840.0 0.0 0 0.00 0.000 2.1 02/04/09 19,213,016.4 211.1 1,840.0 480.3 20 2.00 0.998 0.000 3.7 02/04/09 27,131,065.6 221.9 1,840.0 1,253.3 119 60.00 2.837 0.057 3.4 02/04/09 43,164,645.1 259.2 1,840.02,744.7 246 60.00 3.631 0.159 2.0 02/04/09 39,250,701.4 278.0 1,840.02,879.8 280 60.00 2.892 0.133 2.6 02/04/09 29,536,463.5 270.3 1,840.02,102.8 202 60.00 1.753 0.059 2.9 02/04/09 27,774,276.7 273.0 1,840.0 1,947.2 191 60.00 2.314 0.072 3.2 02/04/09 32,010,666.7 276.8 1,840.02,296.4 221 60.00 2.522 0.093 4.1 02/04/09 33,737,627.7 277.7 1,840.02,420.3 234 60.00 2.783 0.108 3.7 02/04/09 35,711,927.8 282.4 1,840.02,620.2 257 60.00 3.487 0.146 3.1 02/04/09 36,766,011.8 278.3 1,840.02,677.5 260 60.00 3.170 0.136 4.7 02/03/09 35,500,546.6 281.8 1,840.02,585.4 257 60.00 2.656 0.110 02/03/09 40,276,341.1 285.0 1,840.02,955.0 291 60.00 3.997 0.189

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 01:00 02:00 03:00 04:00 05:00 C 06:00 C 07:00 08:00 09:00 C 10:00 C 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 4.1 4.2 02/06/09 25,706,980.6 266.9 1,840.0 1,802.3 179 60.00 3.649 0.105 3.9 02/06/09 25,319,947.6 266.1 1,840.0 1,802.7 179 60.00 3.681 0.106 3.4 02/06/09 25,283,711.9 266.3 1,840.0 1,813.9 179 60.00 3.392 0.098 3.7 02/06/09 25,349,076.9 265.7 1,840.0 1,804.7 179 60.00 2.980 0.086 3.2 02/06/09 25,317,397.9 265.1 1,840.0 1,802.5 179 60.00 3.243 0.093 3.4 02/06/09 25,556,648.0 264.7 1,840.0 1,819.5 179 60.00 2.805 0.082 4.0 02/06/09 25,129,049.8 265.2 1,840.0 1,789.1 179 60.00 2.980 0.085 4.5 02/06/09 26,090,352.6 265.6 1,840.0 1,829.1 183 60.00 3.560 0.104 4.9 02/06/09 26,886,327.8 264.51,840.0 1,899.6 189 60.00 3.974 0.121 5.5 02/06/09 27,471,921.4 264.0 1,840.0 1,970.8 196 60.00 4.262 0.134 5.9 02/06/09 26,346,209.9 260.0 1,840.0 1,904.4 189 60.00 4.748 0.145 3.8 02/06/09 25,466,108.8 246.6 1,840.0 1,674.7 155 60.00 5.598 0.150 2.9 02/06/09 22,357,919.6 225.7 1,840.0 1,239.4 105 60.00 4.277 0.085 2.9 02/06/09 18,421,536.8 215.7 1,840.0 730.9 52 60.00 4.561 0.053 0.0 02/06/09 18,870,496.6 207.9 1,840.0 430.7 21 60.00 7.928 0.055 0.0 02/06/09 19,903,352.2 203.6 1,840.0 400.2 11 60.00 0.000 0.000 0.0 02/06/09 20,227,474.7 201.9 1,840.0 329.8 2 60.00 0.000 0.000 0.0 02/06/09 20,380,230.8 190.51,840.0 265.8 0 60.00 0.000 0.000 0.0 02/06/09 23,016,520.0 177.0 1,840.0 237.7 0 60.00 0.000 0.000 0.0 02/06/09 23,061,901.8 168.1 1,840.0 200.5 0 39.00 0.000 0.000 0.0 02/06/09 22,689,733.9 148.51,840.0 185.0 0 60.00 0.000 0.000 0.0 02/06/09 24,407,651.0 116.6 1,840.0 185.7 0 60.00 0.000 0.000 0.0 02/06/09 23,724,846.9 79.2 1,840.0 128.9 0 60.00 0.000 0.000 0.0 02/06/09 23,435,118.3 66.8 1,840.0 25.5 0 35.00 0.000 0.000 0.0 02/05/09 19,665,013.8 68.6 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 4,255,970.6 68.51,840.0 0.0 0 0.00 0.000 0.0 02/05/09 1,856,753.1 65.0 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 2,049,576.1 66.4 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 2,477,828.0 67.6 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 2,483,009.3 68.6 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 2,484,728.3 69.8 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 2,473,028.8 71.2 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 2,977,266.2 72.9 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,253,862.1 74.6 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,659,242.5 76.0 1,840.0 0.0 0 0.00 0.000 0.0 02/05/09 3,725,707.5 77.2 1,840.0 0.0 0 0.00 0.000 02/05/09 3,747,784.8 78.8 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 1.4 1.6 02/08/09 25,984,183.7 272.3 1,840.0 1,849.9 180 60.00 1.227 0.036 1.6 02/08/09 25,764,491.3 271.8 1,840.0 1,848.3 182 60.00 1.392 0.041 1.3 02/08/09 25,553,323.7 271.6 1,840.0 1,833.2 182 60.00 1.392 0.041 1.5 02/08/09 25,433,656.5 272.0 1,840.0 1,810.8 178 60.00 1.139 0.033 1.6 02/08/09 25,876,612.8 273.2 1,840.0 1,828.3 181 60.00 1.325 0.039 1.6 02/08/09 26,195,513.2 271.51,840.0 1,865.0 183 60.00 1.402 0.042 1.6 02/08/09 25,357,607.0 273.1 1,840.0 1,805.4 181 60.00 1.402 0.040 1.5 02/08/09 26,462,426.3 273.7 1,840.0 1,898.4 185 60.00 1.392 0.042 1.9 02/08/09 26,949,713.2 273.51,840.0 1,918.7 187 60.00 1.315 0.040 2.0 02/08/09 25,239,719.8 271.2 1,840.0 1,810.7 177 60.00 1.653 0.048 2.2 02/08/09 24,983,779.3 270.9 1,840.0 1,778.8 177 60.00 1.753 0.050 2.1 02/08/09 25,218,404.9 272.0 1,840.0 1,795.4 177 60.00 1.928 0.055 1.6 02/08/09 26,310,870.1 273.8 1,840.0 1,873.2 183 60.00 1.841 0.055 2.7 02/07/09 26,401,759.5 273.7 1,840.0 1,851.0 180 60.00 1.424 0.042 2.7 02/07/09 26,418,333.5 273.0 1,840.0 1,866.5 184 60.00 2.385 0.071 2.6 02/07/09 25,593,653.3 271.9 1,840.0 1,808.3 180 60.00 2.385 0.069 2.4 02/07/09 25,680,426.3 271.4 1,840.0 1,814.3 180 60.00 2.296 0.067 2.4 02/07/09 25,799,398.4 271.1 1,840.0 1,822.8 180 60.00 2.120 0.062 2.1 02/07/09 25,756,195.4 272.7 1,840.0 1,819.7 180 60.00 2.120 0.062 2.4 02/07/09 26,799,289.2 273.2 1,840.0 1,878.8 186 60.00 1.869 0.056 2.7 02/07/09 26,691,598.0 272.1 1,840.0 1,856.8 181 60.00 2.153 0.064 2.5 02/07/09 25,511,866.7 271.3 1,840.0 1,788.6 177 60.00 2.403 0.069 2.7 02/07/09 25,989,813.7 272.3 1,840.0 1,808.0 178 60.00 2.242 0.065 3.7 02/07/09 26,304,564.7 272.6 1,840.0 1,829.9 179 60.00 2.422 0.071 4.4 02/07/09 26,005,643.7 271.51,840.0 1,809.1 180 60.00 3.319 0.096 4.1 02/07/09 25,482,388.7 270.7 1,840.0 1,772.7 179 60.00 3.947 0.112 4.0 02/07/09 26,257,894.9 271.7 1,840.0 1,826.6 182 60.00 3.678 0.107 4.2 02/07/09 26,165,432.9 271.7 1,840.0 1,806.0 178 60.00 3.616 0.104 4.5 02/07/09 26,284,727.7 271.51,840.0 1,800.0 177 60.00 3.827 0.110 4.4 02/07/09 25,617,191.7 270.6 1,840.0 1,768.1 177 60.00 4.068 0.115 4.8 02/07/09 26,495,801.8 273.0 1,840.0 1,814.4 182 60.00 4.009 0.116 4.9 02/07/09 26,587,592.1 273.2 1,840.0 1,835.2 178 60.00 4.340 0.127 5.3 02/07/09 26,500,800.8 272.6 1,840.0 1,829.1 176 60.00 4.430 0.130 4.9 02/07/09 25,951,355.0 271.7 1,840.0 1,805.3 178 60.00 4.754 0.137 4.3 02/07/09 26,292,065.3 271.8 1,840.0 1,814.7 179 60.00 4.430 0.129 4.1 02/07/09 26,315,601.5 271.3 1,840.0 1,830.7 179 60.00 3.857 0.113 02/07/09 26,382,301.0 268.7 1,840.0 1,820.9 179 60.00 3.707 0.108

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 1.8 1.9 02/10/09 25,678,542.0 268.9 1,840.0 1,800.3 178 60.00 1.602 0.046 1.3 02/10/09 26,095,636.4 269.0 1,840.0 1,843.7 184 60.00 1.678 0.049 1.9 02/09/09 26,189,313.1 268.51,840.0 1,836.1 184 60.00 1.157 0.034 2.2 02/09/09 25,620,904.1 268.51,840.0 1,796.3 180 60.00 1.691 0.049 2.8 02/09/09 25,996,530.6 268.51,840.0 1,850.9 181 60.00 1.928 0.057 3.2 02/09/09 26,299,159.1 271.1 1,840.0 1,858.1 183 60.00 2.473 0.073 3.5 02/09/09 32,325,882.8 280.9 1,840.02,336.6 231 60.00 2.762 0.103 3.0 02/09/09 38,757,733.2 283.6 1,840.02,843.7 280 60.00 2.977 0.135 2.5 02/09/09 32,850,905.9 273.4 1,840.02,356.7 226 60.00 2.609 0.098 2.6 02/09/09 27,839,684.2 271.6 1,840.0 1,921.6 184 60.00 2.260 0.069 2.5 02/09/09 28,327,619.8 270.9 1,840.0 1,955.2 185 60.00 2.351 0.073 2.5 02/09/09 27,543,171.2 269.51,840.0 1,901.1 181 60.00 2.260 0.069 2.2 02/09/09 27,389,640.5 270.7 1,840.0 1,905.4 187 60.00 2.242 0.068 2.9 02/09/09 27,260,066.8 270.6 1,840.0 1,940.8 187 60.00 1.928 0.060 3.9 02/09/09 28,732,949.1 277.2 1,840.02,061.3 206 60.00 2.522 0.083 3.7 02/09/09 37,710,361.0 284.7 1,840.02,807.8 273 60.00 3.268 0.147 3.8 02/09/09 36,275,190.4 280.8 1,840.02,720.6 262 60.00 3.078 0.134 3.2 02/09/09 36,511,767.1 282.3 1,840.02,738.4 266 60.00 3.162 0.138 2.1 02/09/09 35,196,927.0 278.1 1,840.02,620.6 254 60.00 2.682 0.112 2.0 02/09/09 30,795,435.3 273.0 1,840.02,242.7 217 60.00 1.799 0.065 1.7 02/09/09 27,023,944.0 272.9 1,840.0 1,909.3 186 60.00 1.766 0.054 1.7 02/09/09 27,455,167.2 273.8 1,840.0 1,954.7 190 60.00 1.490 0.047 1.9 02/09/09 26,088,431.9 272.8 1,840.0 1,843.2 179 60.00 1.501 0.044 2.1 02/09/09 25,517,026.8 271.9 1,840.0 1,802.8 177 60.00 1.678 0.048 1.8 02/09/09 25,731,300.6 271.6 1,840.0 1,845.9 182 60.00 1.827 0.054 1.7 02/09/09 26,147,426.9 273.1 1,840.0 1,875.8 184 60.00 1.566 0.047 1.7 02/08/09 26,138,690.6 273.1 1,840.0 1,861.0 181 60.00 1.490 0.044 2.3 02/08/09 26,050,483.7 273.0 1,840.0 1,854.6 180 60.00 1.490 0.044 2.6 02/08/09 25,359,076.5 273.1 1,840.0 1,819.2 179 60.00 2.001 0.058 2.6 02/08/09 28,490,693.1 277.0 1,840.02,105.9 207 60.00 2.195 0.074 2.1 02/08/09 31,173,972.6 277.6 1,840.02,321.1 227 60.00 2.179 0.081 1.5 02/08/09 30,205,536.3 278.7 1,840.02,216.2 219 60.00 1.786 0.063 1.5 02/08/09 28,842,920.1 274.3 1,840.02,084.8 203 60.00 1.295 0.043 1.7 02/08/09 26,321,892.1 272.4 1,840.0 1,888.3 186 60.00 1.305 0.039 1.4 02/08/09 25,348,287.1 271.2 1,840.0 1,832.2 181 60.00 1.468 0.043 1.3 02/08/09 25,528,853.9 271.3 1,840.0 1,845.3 181 60.00 1.209 0.036 02/08/09 25,447,740.5 271.8 1,840.0 1,825.6 178 60.00 1.131 0.033

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 2.7 2.8 02/11/09 27,500,084.4 270.6 1,840.0 1,778.5 181 60.00 2.605 0.074 2.5 02/11/09 29,547,717.1 272.6 1,840.0 1,927.0 197 60.00 2.679 0.083 2.6 02/11/09 29,257,545.1 275.4 1,840.0 1,892.2 195 60.00 2.412 0.073 2.9 02/11/09 31,834,456.6 278.51,840.02,128.0 213 60.00 2.427 0.083 3.3 02/11/09 36,577,270.7 286.51,840.02,564.4 250 60.00 2.581 0.106 2.9 02/11/09 40,008,239.9 288.4 1,840.02,826.7 279 60.00 2.915 0.132 2.7 02/11/09 40,145,601.7 285.7 1,840.02,814.6 275 60.00 2.581 0.116 2.4 02/11/09 39,154,345.8 287.3 1,840.02,745.0 270 60.00 2.403 0.105 2.3 02/11/09 34,024,746.6 277.1 1,840.02,422.4 232 60.00 2.103 0.081 2.2 02/11/09 27,611,302.2 272.6 1,840.0 1,875.7 183 60.00 2.113 0.063 2.2 02/11/09 27,299,430.7 272.7 1,840.0 1,869.4 183 60.00 2.005 0.060 2.2 02/11/09 26,596,355.3 272.1 1,840.0 1,835.7 177 60.00 1.989 0.058 2.3 02/11/09 27,025,666.4 272.4 1,840.0 1,836.0 180 60.00 2.021 0.059 2.2 02/11/09 27,255,324.0 272.1 1,840.0 1,851.6 179 60.00 2.113 0.063 1.8 02/11/09 27,736,526.0 271.4 1,840.0 1,854.2 182 60.00 2.054 0.061 1.7 02/10/09 27,484,657.8 271.4 1,840.0 1,852.3 182 60.00 1.667 0.049 1.8 02/10/09 27,054,570.9 271.9 1,840.0 1,867.4 184 60.00 1.537 0.046 2.1 02/10/09 26,850,083.6 272.2 1,840.0 1,824.0 180 60.00 1.653 0.048 2.2 02/10/09 27,407,500.6 271.9 1,840.0 1,891.7 184 60.00 1.899 0.057 2.1 02/10/09 28,174,017.5 272.9 1,840.0 1,959.9 194 60.00 1.973 0.062 1.9 02/10/09 29,991,334.2 276.9 1,840.02,102.6 210 60.00 1.869 0.063 1.6 02/10/09 30,776,020.5 274.8 1,840.02,258.0 217 60.00 1.616 0.058 1.7 02/10/09 27,061,033.4 271.0 1,840.0 1,970.7 188 60.00 1.371 0.043 1.6 02/10/09 25,811,416.2 269.3 1,840.0 1,851.7 181 60.00 1.479 0.044 1.6 02/10/09 25,102,241.6 269.6 1,840.0 1,800.8 179 60.00 1.392 0.040 1.6 02/10/09 25,780,973.9 270.3 1,840.0 1,821.5 182 60.00 1.413 0.041 1.9 02/10/09 25,777,418.7 270.3 1,840.0 1,793.2 181 60.00 1.435 0.041 1.5 02/10/09 26,091,110.4 269.1 1,840.0 1,857.6 185 60.00 1.665 0.049 1.5 02/10/09 25,030,987.6 268.3 1,840.0 1,782.1 181 60.00 1.315 0.037 1.5 02/10/09 25,571,990.6 269.6 1,840.0 1,806.7 181 60.00 1.325 0.038 1.8 02/10/09 27,300,197.3 270.7 1,840.0 1,914.0 187 60.00 1.335 0.041 1.8 02/10/09 27,070,612.2 273.7 1,840.0 1,912.6 188 60.00 1.590 0.049 1.9 02/10/09 30,156,978.8 271.2 1,840.02,147.0 208 60.00 1.578 0.054 1.7 02/10/09 26,023,023.6 268.7 1,840.0 1,824.4 181 60.00 1.691 0.049 1.6 02/10/09 26,772,003.6 269.8 1,840.0 1,877.0 185 60.00 1.513 0.045 1.6 02/10/09 26,137,242.1 269.4 1,840.0 1,818.2 178 60.00 1.435 0.042 02/10/09 26,018,216.8 269.4 1,840.0 1,781.7 178 60.00 1.458 0.042

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 C 02:00 C C 03:00 C 2.9 6.1 02/13/09 26,778,460.0 269.6 1,840.0 1,819.2 178 60.00 2.664 0.077 2.8 02/13/09 26,523,723.6 270.2 1,840.0 1,773.1 178 60.00 5.694 0.161 2.6 02/13/09 26,611,273.8 271.0 1,840.0 1,851.2 178 60.00 2.512 0.074 2.6 02/13/09 26,934,620.5 271.4 1,840.0 1,903.0 180 60.00 2.296 0.070 2.6 02/12/09 26,686,512.1 272.0 1,840.0 1,885.5 180 60.00 2.296 0.069 2.7 02/12/09 27,266,476.9 273.8 1,840.0 1,926.4 186 60.00 2.296 0.071 3.5 02/12/09 29,724,994.1 278.8 1,840.02,148.6 207 60.00 2.331 0.080 3.8 02/12/09 37,077,969.8 288.51,840.02,680.1 259 60.00 3.021 0.129 3.5 02/12/09 40,591,030.5 291.3 1,840.02,978.1 284 60.00 3.232 0.154 2.9 02/12/09 41,643,872.6 291.4 1,840.03,055.4 291 60.00 2.977 0.145 2.8 02/12/09 33,209,171.4 277.7 1,840.02,400.4 225 60.00 2.504 0.096 2.6 02/12/09 26,825,294.1 273.3 1,840.0 1,953.6 187 60.00 2.399 0.075 2.6 02/12/09 25,690,588.8 273.3 1,840.0 1,871.0 179 60.00 2.228 0.067 3.0 02/12/09 26,384,624.4 274.1 1,840.0 1,878.5 180 60.00 2.279 0.068 3.2 02/12/09 30,793,620.2 282.1 1,840.02,158.9 218 60.00 2.670 0.092 2.7 02/12/09 32,142,063.1 277.0 1,840.02,393.2 224 60.00 2.682 0.103 3.2 02/12/09 27,972,464.1 277.3 1,840.0 1,976.3 194 60.00 2.385 0.075 3.5 02/12/09 34,577,974.7 286.3 1,840.02,461.8 242 60.00 2.805 0.110 3.3 02/12/09 38,851,947.3 288.8 1,840.02,808.3 272 60.00 3.021 0.136 3.3 02/12/09 36,938,295.4 284.6 1,840.02,730.2 259 60.00 2.786 0.122 3.0 02/12/09 32,252,053.1 277.7 1,840.02,243.6 221 60.00 2.960 0.106 2.6 02/12/09 31,345,044.3 273.1 1,840.02,112.4 209 60.00 2.778 0.094 2.6 02/12/09 27,659,599.9 271.8 1,840.0 1,834.0 183 60.00 2.447 0.072 2.6 02/12/09 28,262,637.2 271.51,840.0 1,874.0 184 60.00 2.447 0.073 2.7 02/12/09 27,006,354.2 271.2 1,840.0 1,805.3 177 60.00 2.427 0.070 2.8 02/12/09 26,916,428.5 271.1 1,840.0 1,770.0 177 60.00 2.562 0.073 2.7 02/12/09 27,283,995.6 271.1 1,840.0 1,764.6 177 60.00 2.702 0.076 2.1 02/12/09 28,086,133.5 270.8 1,840.0 1,816.4 182 60.00 2.605 0.076 2.6 02/11/09 27,027,309.3 269.7 1,840.0 1,762.6 179 60.00 2.009 0.057 2.6 02/11/09 27,206,041.9 271.4 1,840.0 1,789.1 180 60.00 2.467 0.071 2.6 02/11/09 27,762,898.5 271.9 1,840.0 1,810.6 182 60.00 2.488 0.072 3.0 02/11/09 27,790,454.0 274.3 1,840.0 1,842.6 185 60.00 2.447 0.072 3.5 02/11/09 30,361,059.7 281.51,840.02,178.1 215 60.00 2.609 0.091 2.7 02/11/09 36,614,881.2 284.9 1,840.02,646.6 254 60.00 3.021 0.128 2.8 02/11/09 31,809,777.2 275.8 1,840.02,091.9 208 60.00 2.562 0.086 2.9 02/11/09 31,121,107.9 275.0 1,840.02,029.6 203 60.00 2.679 0.087 02/11/09 28,721,556.8 271.51,840.0 1,873.2 187 60.00 2.775 0.083

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 2.0 1.7 02/14/09 30,615,178.9 271.7 1,840.02,179.7 203 60.00 1.753 0.061 1.4 02/14/09 26,193,657.5 268.6 1,840.0 1,864.9 174 60.00 1.490 0.044 2.3 02/14/09 25,208,907.5 268.7 1,840.0 1,781.1 165 60.00 1.236 0.035 2.4 02/14/09 25,747,476.2 269.4 1,840.0 1,833.1 173 60.00 2.016 0.059 2.2 02/14/09 27,198,880.9 271.3 1,840.0 1,995.6 188 60.00 2.041 0.065 2.3 02/14/09 29,434,270.2 276.0 1,840.02,095.6 207 60.00 1.928 0.065 2.8 02/14/09 34,446,313.3 280.4 1,840.02,508.6 239 60.00 1.971 0.079 2.2 02/14/09 35,733,741.2 283.4 1,840.02,641.2 255 60.00 2.364 0.100 1.8 02/14/09 32,734,244.6 276.6 1,840.02,366.1 226 60.00 1.899 0.072 1.9 02/14/09 28,565,453.5 270.3 1,840.02,049.2 195 60.00 1.566 0.051 1.5 02/14/09 24,502,264.7 267.8 1,840.0 1,731.1 166 60.00 1.678 0.046 1.3 02/14/09 24,145,423.2 268.4 1,840.0 1,719.0 162 60.00 1.315 0.036 1.4 02/14/09 23,702,639.1 267.6 1,840.0 1,648.9 156 60.00 1.166 0.031 2.1 02/14/09 23,635,157.9 267.8 1,840.0 1,669.9 157 60.00 1.236 0.033 2.0 02/14/09 23,033,481.3 266.7 1,840.0 1,627.3 156 60.00 1.855 0.048 1.7 02/14/09 23,522,426.2 266.4 1,840.0 1,687.4 159 60.00 1.740 0.047 1.5 02/14/09 23,371,929.5 266.6 1,840.0 1,676.7 159 60.00 1.479 0.040 2.5 02/13/09 24,121,384.4 267.7 1,840.0 1,704.2 165 60.00 1.325 0.036 2.1 02/13/09 25,894,540.5 269.2 1,840.0 1,857.7 179 60.00 2.175 0.065 2.3 02/13/09 27,259,650.6 272.8 1,840.0 1,955.6 192 60.00 1.827 0.057 2.2 02/13/09 28,228,463.4 273.2 1,840.02,009.7 197 60.00 2.016 0.065 3.2 02/13/09 28,671,796.3 276.3 1,840.02,056.9 201 60.00 1.914 0.063 2.9 02/13/09 34,399,717.0 280.9 1,840.02,542.6 245 60.00 2.702 0.110 2.4 02/13/09 30,568,479.9 271.2 1,840.02,209.5 211 60.00 2.504 0.088 2.4 02/13/09 25,946,954.4 268.9 1,840.0 1,847.3 180 60.00 2.103 0.062 2.4 02/13/09 26,678,110.0 271.0 1,840.0 1,841.4 184 60.00 2.170 0.064 3.7 02/13/09 27,397,844.5 273.8 1,840.0 1,831.5 183 60.00 2.240 0.066 4.1 02/13/09 34,692,221.6 282.0 1,840.02,469.9 237 60.00 3.243 0.128 4.1 02/13/09 34,962,525.7 283.7 1,840.02,546.2 243 60.00 3.513 0.143 4.5 02/13/09 37,699,713.0 285.3 1,840.02,786.5 263 60.00 3.461 0.154 4.5 02/13/09 39,405,413.9 289.0 1,840.02,891.1 276 60.00 3.827 0.177 4.4 02/13/09 39,538,756.2 288.9 1,840.02,922.4 278 60.00 3.799 0.178 3.8 02/13/09 40,755,616.1 290.1 1,840.02,990.3 287 60.00 3.742 0.179 3.0 02/13/09 40,338,343.1 286.9 1,840.02,959.6 285 60.00 3.232 0.153 2.2 02/13/09 35,047,144.2 276.4 1,840.02,476.1 239 60.00 2.650 0.105 2.6 02/13/09 28,141,707.8 271.8 1,840.02,003.6 194 60.00 1.928 0.062 02/13/09 26,298,371.3 270.51,840.0 1,843.7 179 60.00 2.314 0.068

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 2.4 1.9 02/16/09 30,031,884.3 273.9 1,840.02,138.1 205 60.00 2.103 0.072 2.3 02/16/09 26,603,176.1 270.6 1,840.0 1,908.5 179 60.00 1.653 0.050 2.3 02/16/09 24,367,123.3 268.3 1,840.0 1,748.1 165 60.00 2.001 0.056 2.6 02/16/09 23,136,992.2 268.0 1,840.0 1,634.7 158 60.00 2.031 0.053 2.3 02/16/09 24,061,190.8 269.6 1,840.0 1,752.3 168 60.00 2.228 0.062 1.9 02/16/09 24,491,895.8 269.0 1,840.0 1,810.3 168 60.00 1.942 0.056 2.2 02/15/09 25,666,778.7 271.6 1,840.0 1,883.2 180 60.00 1.616 0.049 2.5 02/15/09 27,207,480.8 271.51,840.0 1,937.0 185 60.00 1.928 0.060 2.7 02/15/09 28,779,240.2 274.3 1,840.02,048.9 197 60.00 2.191 0.072 3.3 02/15/09 30,864,484.4 279.4 1,840.02,247.7 213 60.00 2.313 0.083 3.5 02/15/09 36,342,817.7 285.3 1,840.02,706.0 254 60.00 2.766 0.120 2.7 02/15/09 38,254,915.0 284.6 1,840.02,827.5 269 60.00 2.955 0.134 1.9 02/15/09 30,177,896.6 270.9 1,840.02,181.3 203 60.00 2.331 0.081 2.3 02/15/09 24,860,012.8 267.2 1,840.0 1,729.4 167 60.00 1.704 0.047 2.4 02/15/09 24,414,776.1 268.2 1,840.0 1,711.7 162 60.00 2.047 0.056 2.7 02/15/09 23,932,460.6 268.8 1,840.0 1,703.9 160 60.00 2.103 0.057 3.0 02/15/09 24,210,944.0 268.51,840.0 1,723.7 159 60.00 2.366 0.065 3.0 02/15/09 24,747,699.6 269.4 1,840.0 1,775.4 167 60.00 2.609 0.074 3.0 02/15/09 25,463,366.9 270.2 1,840.0 1,826.7 174 60.00 2.609 0.076 2.9 02/15/09 27,238,681.4 273.9 1,840.0 1,983.7 190 60.00 2.571 0.082 3.5 02/15/09 28,136,835.8 276.8 1,840.02,049.1 195 60.00 2.485 0.081 3.2 02/15/09 34,823,596.8 284.2 1,840.02,555.0 243 60.00 2.977 0.122 3.4 02/15/09 31,584,239.3 276.51,840.02,300.1 213 60.00 2.742 0.101 3.3 02/15/09 26,710,937.9 272.9 1,840.0 1,916.2 183 60.00 2.957 0.091 2.9 02/15/09 26,528,651.9 270.7 1,840.0 1,903.2 180 60.00 2.870 0.087 3.0 02/15/09 23,257,888.2 268.8 1,840.0 1,681.1 158 60.00 2.504 0.067 2.6 02/15/09 24,292,061.5 269.2 1,840.0 1,742.7 165 60.00 2.609 0.073 2.6 02/15/09 24,070,932.7 269.2 1,840.0 1,726.8 161 60.00 2.262 0.062 2.8 02/15/09 24,048,387.4 269.8 1,840.0 1,725.2 161 60.00 2.262 0.062 2.9 02/15/09 24,517,156.7 270.2 1,840.0 1,732.2 163 60.00 2.473 0.068 3.4 02/14/09 24,227,586.2 272.6 1,840.0 1,711.8 164 60.00 2.561 0.070 3.5 02/14/09 28,004,417.2 276.7 1,840.02,069.9 196 60.00 2.870 0.095 3.9 02/14/09 32,038,998.5 281.1 1,840.02,333.3 225 60.00 2.999 0.112 4.0 02/14/09 34,540,515.8 282.1 1,840.02,515.5 243 60.00 3.342 0.134 3.9 02/14/09 35,224,730.1 285.4 1,840.02,641.9 253 60.00 3.328 0.141 2.6 02/14/09 39,182,278.5 286.0 1,840.02,981.2 277 60.00 3.198 0.152 02/14/09 34,478,199.5 277.2 1,840.02,529.6 236 60.00 2.211 0.089

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 3.2 2.6 02/17/09 39,597,054.5 282.7 1,840.02,862.2 280 60.00 2.762 0.126 2.3 02/17/09 32,892,754.5 276.2 1,840.02,341.8 224 60.00 2.279 0.085 2.9 02/17/09 32,270,379.5 278.2 1,840.02,315.0 222 60.00 2.001 0.074 3.6 02/17/09 35,199,478.9 280.4 1,840.02,563.4 242 60.00 2.485 0.102 3.6 02/17/09 36,247,259.7 282.6 1,840.02,679.1 257 60.00 3.039 0.130 3.7 02/17/09 36,882,471.7 282.9 1,840.02,746.1 262 60.00 3.017 0.132 3.2 02/17/09 39,089,093.0 285.51,840.02,889.2 280 60.00 3.124 0.144 3.5 02/17/09 40,456,067.2 285.8 1,840.02,990.2 287 60.00 2.702 0.129 3.5 02/17/09 39,828,925.0 286.51,840.02,943.9 283 60.00 2.955 0.139 3.5 02/17/09 40,581,070.0 286.9 1,840.02,999.5 289 60.00 2.955 0.142 3.1 02/17/09 40,765,450.3 285.3 1,840.03,013.1 290 60.00 2.955 0.142 2.8 02/17/09 38,797,570.3 286.4 1,840.02,867.7 274 60.00 2.617 0.120 2.2 02/17/09 39,386,801.9 285.1 1,840.02,911.2 277 60.00 2.364 0.110 2.6 02/17/09 31,498,477.4 274.4 1,840.02,242.5 207 60.00 1.928 0.069 2.6 02/17/09 24,957,649.3 269.6 1,840.0 1,749.8 165 60.00 2.314 0.065 2.5 02/17/09 24,435,451.1 268.7 1,840.0 1,699.8 163 60.00 2.332 0.063 2.4 02/17/09 23,793,427.8 267.7 1,840.0 1,616.4 163 60.00 2.296 0.059 2.4 02/17/09 23,655,738.6 268.1 1,840.0 1,671.3 159 60.00 2.120 0.057 2.4 02/17/09 24,259,508.3 268.3 1,840.0 1,740.4 163 60.00 2.088 0.058 2.1 02/16/09 24,237,252.1 267.0 1,840.0 1,712.4 161 60.00 2.120 0.058 2.3 02/16/09 24,282,218.2 269.1 1,840.0 1,715.6 164 60.00 1.855 0.051 2.5 02/16/09 27,475,397.0 272.8 1,840.0 1,956.1 187 60.00 2.016 0.063 3.1 02/16/09 30,857,673.4 278.8 1,840.02,213.7 213 60.00 2.175 0.077 3.1 02/16/09 37,011,850.7 283.7 1,840.02,735.7 258 60.00 2.617 0.114 1.7 02/16/09 34,941,268.6 278.2 1,840.02,544.6 244 60.00 2.656 0.108 1.7 02/16/09 28,184,245.1 269.3 1,840.02,006.6 189 60.00 1.490 0.048 2.0 02/16/09 24,568,301.5 270.2 1,840.0 1,722.4 165 60.00 1.513 0.042 2.0 02/16/09 24,277,556.2 270.8 1,840.0 1,781.3 163 60.00 1.701 0.048 2.8 02/16/09 25,453,197.6 271.9 1,840.0 1,826.0 170 60.00 1.740 0.051 2.6 02/16/09 27,042,422.4 272.9 1,840.0 1,984.1 187 60.00 2.381 0.076 2.3 02/16/09 28,285,007.7 275.0 1,840.02,044.5 198 60.00 2.245 0.073 2.4 02/16/09 31,869,111.7 279.1 1,840.02,303.6 222 60.00 1.986 0.073 3.0 02/16/09 32,658,468.5 281.0 1,840.02,342.9 227 60.00 2.088 0.078 3.2 02/16/09 36,939,038.7 286.1 1,840.02,710.2 261 60.00 2.551 0.111 3.4 02/16/09 38,224,461.3 284.51,840.02,825.3 272 60.00 2.702 0.122 2.8 02/16/09 34,836,223.2 280.8 1,840.02,574.8 246 60.00 2.870 0.118 02/16/09 34,610,567.4 279.2 1,840.02,558.2 241 60.00 2.364 0.097

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 2.5 2.2 02/19/09 40,278,549.3 283.1 1,840.02,977.1 289 60.00 2.111 0.100 1.5 02/19/09 35,988,420.0 278.9 1,840.02,660.0 252 60.00 1.857 0.079 1.5 02/19/09 31,018,702.8 269.8 1,840.02,225.3 209 60.00 1.305 0.046 1.4 02/19/09 25,097,854.0 267.3 1,840.0 1,732.3 169 60.00 1.356 0.038 1.1 02/19/09 26,228,480.4 266.6 1,840.0 1,824.6 176 60.00 1.256 0.037 1.1 02/19/09 24,768,839.1 266.0 1,840.0 1,669.2 165 60.00 1.019 0.027 1.0 02/19/09 25,312,495.5 266.7 1,840.0 1,719.6 166 60.00 1.010 0.028 1.4 02/19/09 24,907,691.1 266.4 1,840.0 1,678.6 162 60.00 0.926 0.025 2.1 02/18/09 25,148,133.4 267.3 1,840.0 1,735.8 167 60.00 1.266 0.035 2.8 02/18/09 26,294,207.6 270.9 1,840.0 1,857.7 184 60.00 1.855 0.055 3.4 02/18/09 32,234,902.6 276.8 1,840.02,312.5 229 60.00 2.435 0.090 3.2 02/18/09 36,072,810.1 281.3 1,840.02,627.1 257 60.00 2.913 0.122 2.8 02/18/09 38,337,476.3 281.6 1,840.02,771.1 271 60.00 2.762 0.122 2.6 02/18/09 35,480,071.9 276.8 1,840.02,526.0 246 60.00 2.454 0.099 2.3 02/18/09 32,693,733.1 273.51,840.02,309.9 225 60.00 2.296 0.085 2.4 02/18/09 31,610,692.7 271.7 1,840.02,216.2 212 60.00 2.047 0.073 2.6 02/18/09 30,998,012.1 272.6 1,840.02,156.4 208 60.00 2.153 0.074 2.7 02/18/09 29,295,657.1 270.51,840.02,038.0 197 60.00 2.332 0.076 3.4 02/18/09 30,274,834.0 279.3 1,840.02,155.4 212 60.00 2.366 0.082 3.4 02/18/09 38,495,108.1 284.3 1,840.02,824.4 271 60.00 2.892 0.131 3.5 02/18/09 37,464,114.4 284.7 1,840.02,728.4 262 60.00 2.913 0.127 3.2 02/18/09 38,164,669.9 283.8 1,840.02,779.4 269 60.00 2.999 0.133 2.6 02/18/09 35,086,673.5 279.8 1,840.02,479.0 240 60.00 2.826 0.112 2.2 02/18/09 32,805,796.1 273.1 1,840.02,300.0 219 60.00 2.314 0.085 2.1 02/18/09 28,298,600.6 275.51,840.0 1,922.5 192 60.00 2.021 0.062 2.1 02/18/09 31,181,519.5 273.1 1,840.02,135.3 204 60.00 1.914 0.065 2.3 02/18/09 28,010,221.5 270.2 1,840.0 1,887.6 181 60.00 1.944 0.059 2.4 02/18/09 24,697,895.6 268.3 1,840.0 1,731.5 164 60.00 2.047 0.057 2.2 02/18/09 24,539,841.8 268.6 1,840.0 1,720.5 163 60.00 2.136 0.059 2.3 02/18/09 25,152,077.9 268.0 1,840.0 1,736.0 162 60.00 1.989 0.055 1.6 02/18/09 24,356,034.8 268.8 1,840.0 1,694.3 161 60.00 2.063 0.056 1.4 02/18/09 25,220,744.0 268.7 1,840.0 1,713.4 163 60.00 1.470 0.040 2.6 02/17/09 24,377,071.4 269.8 1,840.0 1,656.0 160 60.00 1.286 0.034 3.0 02/17/09 27,585,933.6 274.51,840.0 1,949.0 187 60.00 2.296 0.072 3.5 02/17/09 32,967,719.6 282.2 1,840.02,329.3 233 60.00 2.650 0.099 3.5 02/17/09 39,372,636.3 286.7 1,840.02,846.0 280 60.00 3.021 0.138 02/17/09 39,894,848.5 287.1 1,840.02,883.7 285 60.00 3.021 0.139

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 C 02:00 C S S SC 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 3.0 2.9 02/20/09 37,887,632.5 284.9 1,840.02,779.8 269 60.00 2.551 0.113 2.7 02/20/09 41,108,106.8 285.3 1,840.02,993.7 295 60.00 2.485 0.119 2.3 02/20/09 40,305,721.7 284.51,840.02,935.3 286 60.00 2.313 0.109 2.6 02/20/09 37,307,079.8 281.9 1,840.02,737.2 261 60.00 1.956 0.086 3.0 02/20/09 39,227,612.3 282.7 1,840.02,878.1 276 60.00 2.211 0.102 2.5 02/20/09 36,074,161.4 280.8 1,840.02,646.7 253 60.00 2.551 0.108 2.4 02/20/09 36,888,135.2 280.0 1,840.02,726.5 260 60.00 2.111 0.092 2.3 02/20/09 35,889,987.1 280.8 1,840.02,652.7 250 60.00 2.026 0.086 2.3 02/20/09 37,339,379.3 280.6 1,840.02,759.8 260 60.00 1.942 0.086 3.7 02/20/09 37,339,489.0 282.1 1,840.02,739.5 262 60.00 1.956 0.086 3.8 02/20/09 39,984,152.3 284.3 1,840.02,955.3 285 60.00 3.124 0.148 3.5 02/20/09 41,147,940.3 284.9 1,840.03,019.0 295 60.00 3.232 0.156 3.1 02/20/09 41,094,727.4 285.1 1,840.03,037.5 292 60.00 2.955 0.144 2.0 02/20/09 41,532,353.7 284.3 1,840.03,047.2 295 60.00 2.637 0.128 1.2 02/20/09 37,268,779.2 276.9 1,840.02,734.4 259 60.00 1.701 0.074 1.1 02/20/09 30,967,620.7 271.7 1,840.02,238.4 212 60.00 1.036 0.037 1.6 02/20/09 27,339,674.5 268.9 1,840.0 1,916.8 183 60.00 0.979 0.030 12.5 02/20/09 28,957,948.6 275.1 1,840.02,061.7 204 60.00 1.402 0.046 1.4 02/20/09 34,620,067.4 278.4 1,840.02,521.2 242 60.00 10.710 0.432 1.8 02/20/09 35,249,983.4 277.51,840.02,643.8 248 60.00 1.165 0.049 12.5 02/20/09 33,795,667.9 277.8 1,840.02,534.7 236 60.00 1.498 0.061 2.5 02/19/09 37,679,977.5 283.6 1,840.02,826.0 271 60.00 10.400 0.470 3.3 02/19/09 37,597,841.0 281.0 1,840.02,840.3 268 60.00 2.065 0.094 3.3 02/19/09 39,222,152.3 284.3 1,840.02,984.3 286 60.00 2.706 0.129 3.8 02/19/09 40,152,067.7 285.4 1,840.03,055.0 292 60.00 2.706 0.132 3.4 02/19/09 40,437,168.1 285.8 1,840.03,054.8 292 60.00 3.139 0.153 2.5 02/19/09 40,352,977.0 282.51,840.03,048.4 288 60.00 2.808 0.137 2.5 02/19/09 31,379,498.5 271.1 1,840.02,268.2 215 60.00 2.158 0.078 2.4 02/19/09 29,552,176.8 272.0 1,840.02,168.2 210 60.00 2.126 0.074 3.3 02/19/09 32,570,050.9 276.51,840.02,354.2 230 60.00 2.072 0.078 3.6 02/19/09 36,562,979.7 281.8 1,840.02,682.6 260 60.00 2.807 0.120 3.5 02/19/09 39,576,440.9 283.7 1,840.02,903.7 282 60.00 3.062 0.142 3.6 02/19/09 37,976,389.3 281.0 1,840.02,806.9 270 60.00 2.955 0.133 3.6 02/19/09 36,675,772.6 281.6 1,840.02,710.8 263 60.00 3.039 0.132 3.5 02/19/09 40,867,927.5 285.1 1,840.03,020.7 297 60.00 3.039 0.147 3.4 02/19/09 40,549,025.5 284.7 1,840.02,997.1 292 60.00 2.955 0.142 02/19/09 40,402,042.1 285.3 1,840.02,986.2 293 60.00 2.870 0.137

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 3.2 3.1 02/22/09 41,037,967.6 285.1 1,840.03,055.5 294 60.00 2.682 0.131 2.7 02/22/09 40,648,121.3 284.6 1,840.03,026.5 290 60.00 2.598 0.126 3.1 02/22/09 37,116,007.8 280.51,840.02,763.5 262 60.00 2.263 0.100 3.1 02/22/09 38,691,584.9 284.51,840.02,880.9 276 60.00 2.598 0.120 2.9 02/22/09 38,937,699.3 282.7 1,840.02,920.4 277 60.00 2.579 0.120 2.9 02/22/09 37,213,236.8 281.1 1,840.02,791.0 265 60.00 2.413 0.108 2.9 02/22/09 37,357,762.9 281.8 1,840.02,761.2 264 60.00 2.448 0.108 2.9 02/22/09 38,604,454.7 283.1 1,840.02,832.4 273 60.00 2.466 0.112 3.0 02/22/09 38,402,156.0 282.51,840.02,838.4 273 60.00 2.448 0.111 12.5 02/22/09 38,347,942.6 281.2 1,840.02,855.3 274 60.00 2.514 0.115 3.3 02/21/09 36,990,456.1 282.3 1,840.02,734.0 263 60.00 10.553 0.461 3.5 02/21/09 39,302,125.3 284.2 1,840.02,926.3 280 60.00 2.766 0.129 3.6 02/21/09 39,790,867.7 285.9 1,840.02,962.7 284 60.00 2.933 0.139 3.4 02/21/09 41,519,938.6 287.2 1,840.03,068.9 296 60.00 3.039 0.149 2.9 02/21/09 41,697,139.7 286.1 1,840.03,059.3 297 60.00 2.892 0.141 2.4 02/21/09 40,955,927.3 284.8 1,840.02,982.7 291 60.00 2.485 0.119 2.6 02/21/09 37,355,947.6 277.6 1,840.02,659.6 254 60.00 2.103 0.089 2.8 02/21/09 34,101,664.5 278.1 1,840.02,465.0 239 60.00 2.245 0.088 3.1 02/21/09 37,000,923.7 280.0 1,840.02,694.6 261 60.00 2.399 0.103 3.1 02/21/09 39,622,927.0 284.7 1,840.02,885.6 283 60.00 2.656 0.123 2.8 02/21/09 40,392,479.4 284.4 1,840.02,963.5 288 60.00 2.637 0.125 2.7 02/21/09 40,813,051.7 284.9 1,840.02,994.4 292 60.00 2.381 0.114 2.6 02/21/09 39,556,623.6 283.6 1,840.02,945.3 285 60.00 2.263 0.107 2.2 02/21/09 40,379,714.8 285.4 1,840.02,984.6 287 60.00 2.195 0.105 1.8 02/21/09 37,113,110.0 280.9 1,840.02,723.0 259 60.00 1.871 0.081 1.9 02/21/09 35,723,408.1 276.7 1,840.02,562.7 242 60.00 1.566 0.064 1.9 02/21/09 29,978,716.5 273.6 1,840.02,134.4 206 60.00 1.665 0.057 1.6 02/21/09 29,778,568.7 270.7 1,840.02,104.0 202 60.00 1.678 0.056 1.7 02/21/09 27,479,877.8 268.3 1,840.0 1,941.5 186 60.00 1.413 0.044 1.9 02/21/09 25,811,203.7 269.4 1,840.0 1,837.6 175 60.00 1.490 0.044 1.9 02/21/09 27,300,911.0 272.3 1,840.0 1,899.2 186 60.00 1.704 0.052 2.4 02/21/09 30,340,090.6 273.7 1,840.02,110.6 203 60.00 1.704 0.058 2.5 02/21/09 32,814,352.3 278.2 1,840.02,336.2 229 60.00 2.103 0.079 2.7 02/21/09 34,817,143.8 279.0 1,840.02,535.6 245 60.00 2.142 0.087 2.3 02/20/09 35,626,741.7 281.1 1,840.02,613.9 249 60.00 2.296 0.096 2.8 02/20/09 35,175,817.5 280.7 1,840.02,580.8 244 60.00 1.956 0.081 02/20/09 38,442,004.9 283.51,840.02,820.5 272 60.00 2.381 0.107

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 1.6 2.1 02/23/09 38,396,214.1 281.3 1,840.02,900.6 271 60.00 1.322 0.061 2.3 02/23/09 38,070,692.4 283.6 1,840.02,896.7 270 60.00 1.722 0.080 2.1 02/23/09 40,488,711.5 286.2 1,840.03,102.7 290 60.00 1.873 0.093 1.8 02/23/09 41,056,465.9 285.7 1,840.03,168.5 297 60.00 1.698 0.086 1.6 02/23/09 40,829,855.0 285.0 1,840.03,128.8 291 60.00 1.466 0.073 1.6 02/23/09 38,106,555.9 280.7 1,840.02,899.4 268 60.00 1.312 0.061 1.6 02/23/09 36,918,139.2 280.7 1,840.02,788.9 260 60.00 1.322 0.059 1.4 02/23/09 36,712,186.0 279.9 1,840.02,793.3 260 60.00 1.312 0.059 1.5 02/23/09 37,678,372.6 281.9 1,840.02,887.3 269 60.00 1.140 0.053 1.7 02/23/09 38,455,209.2 282.1 1,840.02,925.9 273 60.00 1.230 0.058 1.8 02/23/09 39,047,153.2 284.3 1,840.02,971.0 278 60.00 1.394 0.066 2.1 02/23/09 40,758,192.8 286.3 1,840.03,123.3 294 60.00 1.466 0.073 2.6 02/23/09 41,137,531.7 287.7 1,840.03,152.4 296 60.00 1.710 0.086 2.5 02/23/09 41,644,415.8 287.0 1,840.03,191.2 299 60.00 2.117 0.108 2.4 02/23/09 41,005,910.3 285.3 1,840.03,120.0 298 60.00 2.050 0.102 2.5 02/23/09 41,192,159.7 285.4 1,840.03,156.6 298 60.00 1.954 0.099 2.5 02/23/09 41,291,742.9 284.8 1,840.03,141.8 298 60.00 2.050 0.103 2.4 02/23/09 38,956,863.5 280.7 1,840.02,942.9 280 60.00 2.065 0.097 2.4 02/23/09 35,732,109.1 277.3 1,840.02,679.9 253 60.00 1.997 0.086 2.4 02/23/09 36,922,827.9 279.3 1,840.02,769.2 261 60.00 1.997 0.088 2.3 02/23/09 36,956,511.2 279.0 1,840.02,731.6 259 60.00 2.026 0.089 2.2 02/23/09 36,418,492.1 278.8 1,840.02,711.6 256 60.00 1.928 0.084 2.4 02/23/09 35,629,721.2 276.3 1,840.02,672.3 249 60.00 1.830 0.078 2.8 02/22/09 34,046,353.1 280.51,840.02,534.9 243 60.00 2.011 0.082 2.9 02/22/09 39,061,824.3 282.9 1,840.02,950.9 279 60.00 2.313 0.109 3.2 02/22/09 38,760,916.8 285.2 1,840.02,886.0 275 60.00 2.430 0.112 3.1 02/22/09 41,325,261.2 286.9 1,840.03,121.8 297 60.00 2.643 0.132 3.1 02/22/09 41,281,681.4 286.7 1,840.03,118.6 297 60.00 2.561 0.128 2.9 02/22/09 41,621,471.8 286.7 1,840.03,121.6 298 60.00 2.579 0.129 3.1 02/22/09 39,916,428.1 283.51,840.02,993.7 283 60.00 2.413 0.116 2.8 02/22/09 38,077,528.5 281.8 1,840.02,855.9 271 60.00 2.579 0.118 2.9 02/22/09 38,083,923.8 281.6 1,840.02,835.6 269 60.00 2.347 0.106 2.8 02/22/09 38,069,920.6 282.2 1,840.02,834.6 268 60.00 2.430 0.110 3.0 02/22/09 37,899,203.4 281.7 1,840.02,821.8 267 60.00 2.347 0.106 3.0 02/22/09 38,752,791.0 283.4 1,840.02,906.5 275 60.00 2.496 0.116 3.1 02/22/09 38,895,285.3 283.0 1,840.02,896.0 276 60.00 2.514 0.116 02/22/09 39,283,405.4 284.1 1,840.02,903.5 279 60.00 2.617 0.122

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 S S S 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 2.3 2.2 02/25/09 37,358,736.6 280.6 1,840.02,761.3 260 60.00 1.942 0.086 1.9 02/25/09 37,014,164.3 279.8 1,840.02,715.7 254 60.00 1.871 0.081 1.7 02/25/09 36,372,067.7 279.4 1,840.02,668.6 249 60.00 1.616 0.069 2.0 02/25/09 35,434,642.6 279.6 1,840.02,580.6 240 60.00 1.457 0.060 1.7 02/25/09 36,361,091.5 278.2 1,840.02,608.5 247 60.00 1.740 0.073 1.1 02/25/09 30,149,109.8 269.2 1,840.02,146.5 202 60.00 1.490 0.051 0.9 02/25/09 25,993,427.7 265.4 1,840.0 1,808.2 173 60.00 0.987 0.029 0.6 02/25/09 25,235,247.5 264.9 1,840.0 1,728.0 168 60.00 0.820 0.023 0.4 02/25/09 23,895,425.5 264.51,840.0 1,623.3 159 60.00 0.551 0.014 0.6 02/25/09 24,988,332.3 265.4 1,840.0 1,656.8 162 60.00 0.376 0.010 1.1 02/25/09 25,101,716.4 267.7 1,840.0 1,691.7 165 60.00 0.556 0.015 1.5 02/25/09 28,231,555.4 270.0 1,840.0 1,964.0 188 60.00 0.987 0.031 2.2 02/24/09 28,761,886.9 274.8 1,840.02,032.1 199 60.00 1.325 0.043 2.4 02/24/09 35,520,090.5 279.2 1,840.02,606.1 247 60.00 1.871 0.078 2.3 02/24/09 35,396,267.2 279.7 1,840.02,597.0 248 60.00 2.041 0.085 2.6 02/24/09 37,786,503.7 283.0 1,840.02,751.9 266 60.00 1.971 0.087 2.7 02/24/09 39,753,816.7 285.1 1,840.02,938.3 282 60.00 2.195 0.103 2.5 02/24/09 39,721,862.2 284.8 1,840.02,957.6 282 60.00 2.263 0.107 2.3 02/24/09 35,173,594.9 278.6 1,840.02,599.8 247 60.00 2.111 0.088 2.2 02/24/09 34,033,539.3 278.3 1,840.02,515.6 238 60.00 1.942 0.078 2.1 02/24/09 35,650,840.2 279.4 1,840.02,654.4 251 60.00 1.844 0.078 2.2 02/24/09 36,914,291.9 281.3 1,840.02,748.5 261 60.00 1.760 0.077 2.3 02/24/09 38,243,416.4 283.0 1,840.02,826.7 269 60.00 1.857 0.084 2.0 02/24/09 38,667,955.9 283.3 1,840.02,858.1 273 60.00 1.942 0.089 2.4 02/24/09 38,658,802.0 283.7 1,840.02,857.4 273 60.00 1.688 0.077 2.6 02/24/09 39,910,233.2 286.0 1,840.02,971.6 286 60.00 2.011 0.096 2.4 02/24/09 41,095,209.3 287.0 1,840.03,104.5 295 60.00 2.148 0.107 2.3 02/24/09 40,019,157.8 283.51,840.03,001.4 284 60.00 1.997 0.096 2.0 02/24/09 38,644,691.8 283.51,840.02,877.4 273 60.00 1.928 0.089 1.4 02/24/09 37,566,740.5 278.3 1,840.02,756.3 259 60.00 1.701 0.075 1.5 02/24/09 32,426,949.0 272.6 1,840.02,308.7 217 60.00 1.227 0.045 1.2 02/24/09 32,755,651.8 274.3 1,840.02,367.7 225 60.00 1.295 0.049 1.4 02/24/09 32,191,347.0 273.6 1,840.02,344.3 217 60.00 1.028 0.039 12.5 02/24/09 29,351,673.4 272.7 1,840.02,121.6 199 60.00 1.209 0.041 12.5 02/24/09 33,038,426.4 276.4 1,840.02,406.0 228 60.00 10.710 0.412 12.5 02/24/09 31,580,187.9 274.2 1,840.02,334.2 217 60.00 10.553 0.394 02/23/09 35,777,333.6 281.7 1,840.02,702.7 254 60.00 10.325 0.446

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 0.5 0.6 02/27/09 26,917,449.5 265.3 1,840.0 1,843.2 178 60.00 0.456 0.013 0.8 02/26/09 29,725,090.7 270.51,840.02,084.0 201 60.00 0.534 0.018 1.3 02/26/09 34,085,041.1 273.2 1,840.02,445.2 232 60.00 0.696 0.027 1.7 02/26/09 36,349,705.6 278.1 1,840.02,627.5 254 60.00 1.122 0.047 1.8 02/26/09 39,277,278.2 281.1 1,840.02,881.7 277 60.00 1.446 0.067 1.9 02/26/09 40,324,528.7 283.1 1,840.02,980.5 286 60.00 1.520 0.072 1.7 02/26/09 41,231,096.5 284.2 1,840.03,047.5 296 60.00 1.604 0.078 1.5 02/26/09 40,969,647.9 282.6 1,840.03,006.0 294 60.00 1.446 0.069 1.2 02/26/09 39,774,669.1 281.7 1,840.02,918.3 282 60.00 1.276 0.060 1.8 02/26/09 38,051,183.7 281.1 1,840.02,812.5 268 60.00 1.013 0.046 1.7 02/26/09 40,019,797.7 282.7 1,840.02,936.3 279 60.00 1.531 0.072 1.8 02/26/09 39,834,412.5 284.9 1,840.02,965.9 279 60.00 1.425 0.068 1.9 02/26/09 40,304,184.8 283.4 1,840.02,935.2 281 60.00 1.542 0.072 2.4 02/26/09 40,717,099.5 284.9 1,840.02,921.0 284 60.00 1.653 0.077 2.3 02/26/09 40,754,376.0 284.7 1,840.02,990.1 288 60.00 2.041 0.098 2.2 02/26/09 39,995,867.7 282.4 1,840.02,956.2 284 60.00 1.942 0.092 2.2 02/26/09 39,237,265.8 282.9 1,840.02,878.8 276 60.00 1.871 0.086 2.0 02/26/09 38,333,265.3 281.4 1,840.02,812.5 267 60.00 1.871 0.084 1.8 02/26/09 37,651,180.9 281.1 1,840.02,742.0 261 60.00 1.714 0.075 1.2 02/26/09 34,816,354.3 276.3 1,840.02,535.5 237 60.00 1.542 0.063 0.9 02/26/09 31,458,709.2 270.9 1,840.02,239.7 214 60.00 1.052 0.038 1.0 02/26/09 28,205,298.4 268.2 1,840.0 1,992.7 188 60.00 0.795 0.025 1.3 02/26/09 27,478,238.6 269.2 1,840.0 1,896.6 179 60.00 0.904 0.027 2.0 02/26/09 28,202,065.3 270.9 1,840.0 1,961.9 189 60.00 1.166 0.037 12.5 02/26/09 31,095,847.5 275.0 1,840.02,197.0 215 60.00 1.766 0.062 2.0 02/25/09 32,211,670.2 275.4 1,840.02,310.9 223 60.00 10.873 0.402 2.6 02/25/09 34,432,035.0 279.0 1,840.02,507.5 236 60.00 1.714 0.069 2.5 02/25/09 36,982,958.4 281.4 1,840.02,713.4 254 60.00 2.211 0.096 3.4 02/25/09 36,549,886.5 281.51,840.02,681.7 251 60.00 2.126 0.091 3.2 02/25/09 39,293,460.3 285.6 1,840.02,925.6 276 60.00 2.849 0.133 2.4 02/25/09 40,747,734.9 285.0 1,840.03,011.8 287 60.00 2.702 0.130 2.5 02/25/09 36,637,015.4 277.9 1,840.02,688.0 253 60.00 2.041 0.088 2.0 02/25/09 34,948,371.0 276.8 1,840.02,545.1 240 60.00 2.142 0.087 1.8 02/25/09 35,066,048.6 277.0 1,840.02,534.7 237 60.00 1.727 0.070 2.3 02/25/09 35,108,087.5 279.0 1,840.02,537.7 241 60.00 1.554 0.063 2.8 02/25/09 35,846,517.2 278.1 1,840.02,591.1 243 60.00 1.986 0.082 02/25/09 36,061,724.5 279.3 1,840.02,665.5 252 60.00 2.364 0.101

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 C 02:00 C S S SC 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 1.2 1.1 02/28/09 38,919,499.9 279.9 1,840.02,749.7 268 60.00 1.060 0.047 1.5 02/28/09 38,696,434.1 279.9 1,840.02,734.0 267 60.00 0.972 0.042 1.9 02/28/09 39,949,261.8 281.6 1,840.02,844.2 276 60.00 1.315 0.060 1.3 02/28/09 40,492,896.0 281.1 1,840.02,882.9 281 60.00 1.665 0.077 1.2 02/28/09 40,412,405.0 279.9 1,840.02,877.2 282 60.00 1.139 0.052 1.2 02/28/09 40,893,489.6 280.1 1,840.02,933.6 285 60.00 1.044 0.049 1.2 02/28/09 37,831,667.4 277.0 1,840.02,714.0 260 60.00 1.044 0.045 1.4 02/28/09 36,304,793.3 276.3 1,840.02,604.5 249 60.00 1.044 0.043 1.1 02/28/09 37,006,948.8 278.6 1,840.02,675.0 258 60.00 1.209 0.052 0.9 02/28/09 36,965,979.4 279.1 1,840.02,752.4 259 60.00 0.922 0.041 1.1 02/28/09 36,440,314.1 279.0 1,840.02,693.4 254 60.00 0.760 0.033 0.9 02/28/09 37,364,657.1 277.7 1,840.02,721.1 261 60.00 0.943 0.041 0.6 02/28/09 37,024,115.6 276.9 1,840.02,716.4 259 60.00 0.765 0.033 12.5 02/28/09 35,985,559.0 276.51,840.02,659.8 252 60.00 0.507 0.022 0.9 02/27/09 37,247,079.7 277.4 1,840.02,753.0 260 60.00 10.553 0.465 1.1 02/27/09 36,158,114.0 276.1 1,840.02,672.5 251 60.00 0.760 0.032 1.1 02/27/09 37,461,767.5 277.6 1,840.02,789.3 265 60.00 0.922 0.041 0.9 02/27/09 39,189,508.6 279.51,840.02,918.0 279 60.00 0.922 0.043 1.0 02/27/09 40,306,721.8 280.7 1,840.03,023.0 285 60.00 0.749 0.036 1.2 02/27/09 40,424,526.7 280.8 1,840.03,009.9 286 60.00 0.838 0.040 1.5 02/27/09 37,698,615.5 277.51,840.02,806.9 264 60.00 1.006 0.045 1.3 02/27/09 39,716,132.7 280.4 1,840.02,978.7 282 60.00 1.248 0.059 1.0 02/27/09 39,103,666.1 279.4 1,840.02,932.8 276 60.00 1.082 0.051 1.2 02/27/09 38,802,057.8 279.6 1,840.02,889.1 273 60.00 0.838 0.039 1.2 02/27/09 40,312,627.0 280.7 1,840.03,023.5 286 60.00 0.998 0.048 1.1 02/27/09 40,612,875.1 281.51,840.03,046.0 287 60.00 0.998 0.049 1.1 02/27/09 40,511,057.8 281.3 1,840.03,016.3 286 60.00 0.922 0.044 1.1 02/27/09 40,461,203.3 281.2 1,840.03,012.6 286 60.00 0.922 0.044 1.4 02/27/09 40,419,712.1 281.4 1,840.03,031.5 288 60.00 0.915 0.044 1.2 02/27/09 40,579,142.8 282.0 1,840.03,021.4 287 60.00 1.173 0.057 1.0 02/27/09 40,736,309.6 281.51,840.03,033.1 288 60.00 1.006 0.049 0.8 02/27/09 38,492,584.8 278.2 1,840.02,887.0 271 60.00 0.832 0.038 0.6 02/27/09 35,895,366.7 275.4 1,840.02,614.1 245 60.00 0.685 0.029 0.5 02/27/09 33,918,838.4 271.7 1,840.02,451.8 228 60.00 0.518 0.020 12.5 02/27/09 28,200,765.1 265.7 1,840.0 1,931.2 185 60.00 0.456 0.014 0.2 02/27/09 28,016,250.6 263.9 1,840.0 1,918.5 188 60.00 11.390 0.349 02/27/09 25,718,432.8 263.7 1,840.0 1,775.1 171 60.00 0.181 0.005

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 S S S 02:00 C 2.8 12.5 03/02/09 36,290,414.5 275.6 1,840.02,642.9 251 60.00 2.399 0.101 12.5 03/02/09 33,860,425.1 274.0 1,840.02,465.9 234 60.00 10.710 0.422 12.5 03/02/09 34,801,787.6 274.9 1,840.02,553.4 243 60.00 10.631 0.434 3.2 03/01/09 35,037,158.4 275.6 1,840.02,608.7 245 60.00 10.476 0.437 3.1 03/01/09 39,286,358.0 281.4 1,840.02,925.1 278 60.00 2.682 0.125 3.4 03/01/09 39,826,952.1 281.1 1,840.02,965.4 282 60.00 2.598 0.123 3.6 03/01/09 39,932,816.3 282.0 1,840.02,951.6 283 60.00 2.870 0.135 3.4 03/01/09 40,399,901.0 281.2 1,840.03,030.0 287 60.00 2.995 0.145 2.7 03/01/09 39,687,948.3 280.6 1,840.02,976.6 283 60.00 2.829 0.135 2.2 03/01/09 37,416,364.6 275.9 1,840.02,724.9 257 60.00 2.313 0.101 2.1 03/01/09 33,687,219.4 272.2 1,840.02,435.0 226 60.00 1.899 0.074 2.4 03/01/09 28,436,754.5 268.0 1,840.02,055.5 190 60.00 1.813 0.060 2.2 03/01/09 31,756,458.6 273.2 1,840.02,312.7 221 60.00 2.056 0.076 2.3 03/01/09 35,395,654.8 275.7 1,840.02,577.8 243 60.00 1.885 0.078 2.0 03/01/09 36,914,312.9 278.6 1,840.02,668.2 256 60.00 1.986 0.085 2.0 03/01/09 39,137,602.0 280.3 1,840.02,871.5 274 60.00 1.701 0.078 1.7 03/01/09 39,496,355.7 279.6 1,840.02,919.3 278 60.00 1.688 0.079 1.7 03/01/09 39,246,949.8 280.2 1,840.02,858.2 272 60.00 1.457 0.067 1.3 03/01/09 39,014,143.2 279.9 1,840.02,841.2 270 60.00 1.457 0.066 1.8 03/01/09 36,602,576.1 276.1 1,840.02,665.7 249 60.00 1.114 0.047 2.2 03/01/09 34,886,313.3 277.0 1,840.02,521.7 239 60.00 1.554 0.063 1.8 03/01/09 38,320,749.2 279.51,840.02,769.9 266 60.00 1.899 0.084 1.9 03/01/09 37,981,048.6 278.2 1,840.02,745.4 261 60.00 1.554 0.068 2.3 03/01/09 34,998,717.9 274.4 1,840.02,510.8 234 60.00 1.653 0.066 2.0 03/01/09 35,291,214.3 279.4 1,840.02,531.7 248 60.00 2.001 0.081 1.6 03/01/09 37,014,043.8 276.0 1,840.02,655.4 251 60.00 1.740 0.074 1.5 03/01/09 34,535,481.2 276.0 1,840.02,496.3 238 60.00 1.381 0.055 1.5 02/28/09 35,878,867.9 277.8 1,840.02,612.9 247 60.00 1.285 0.054 1.9 02/28/09 36,698,645.2 278.8 1,840.02,672.6 253 60.00 1.285 0.055 2.4 02/28/09 37,739,761.4 281.8 1,840.02,769.0 262 60.00 1.616 0.072 2.3 02/28/09 39,150,008.7 282.8 1,840.02,915.0 276 60.00 2.011 0.094 2.0 02/28/09 40,691,944.2 283.51,840.03,007.7 287 60.00 1.942 0.093 1.6 02/28/09 40,506,503.6 281.3 1,840.02,972.0 284 60.00 1.701 0.081 1.7 02/28/09 37,983,178.7 278.8 1,840.02,683.6 260 60.00 1.413 0.061 1.3 02/28/09 38,854,469.8 278.51,840.02,745.1 265 60.00 1.501 0.066 1.2 02/28/09 36,260,473.7 277.3 1,840.02,542.1 245 60.00 1.157 0.047 02/28/09 37,603,116.6 277.6 1,840.02,656.7 258 60.00 1.060 0.045

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 * * 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 2.8 2.7 03/03/09 37,979,776.4 277.8 1,840.02,786.6 262 60.00 2.381 0.106 3.3 03/03/09 36,795,343.5 278.3 1,840.02,699.6 253 60.00 2.296 0.099 3.8 03/03/09 38,533,419.7 279.9 1,840.02,869.0 268 60.00 2.766 0.127 2.9 03/03/09 39,299,751.9 280.0 1,840.02,947.5 277 60.00 3.162 0.149 2.7 03/03/09 39,597,039.4 280.51,840.02,969.8 278 60.00 2.413 0.115 2.8 03/03/09 39,283,954.2 280.7 1,840.02,924.9 278 60.00 2.263 0.106 3.0 03/03/09 39,433,093.1 281.0 1,840.02,914.6 278 60.00 2.364 0.110 3.1 03/03/09 39,434,370.1 280.8 1,840.02,914.7 278 60.00 2.533 0.118 3.0 03/03/09 39,362,505.3 280.51,840.02,909.4 279 60.00 2.617 0.122 1.9 03/03/09 39,922,307.4 279.4 1,840.02,950.8 281 60.00 2.533 0.120 1.6 03/03/09 33,270,399.7 269.0 1,840.02,441.0 223 60.00 1.616 0.063 1.4 03/03/09 26,196,968.4 266.7 1,840.0 1,850.9 179 60.00 1.413 0.042 1.8 03/03/09 26,958,153.1 265.6 1,840.0 1,875.3 181 60.00 1.256 0.038 2.5 03/03/09 25,673,408.5 269.9 1,840.0 1,785.9 177 60.00 1.615 0.046 3.2 03/03/09 31,410,971.3 271.3 1,840.02,270.5 213 60.00 2.158 0.078 3.7 03/03/09 32,696,984.8 277.1 1,840.02,399.0 227 60.00 2.722 0.104 3.4 03/02/09 38,961,861.8 281.0 1,840.02,922.2 278 60.00 3.078 0.144 3.2 03/02/09 39,857,624.1 282.3 1,840.02,989.4 283 60.00 2.829 0.135 3.4 03/02/09 39,816,534.8 282.3 1,840.02,986.3 281 60.00 2.662 0.127 3.4 03/02/09 39,499,213.7 281.8 1,840.02,941.0 277 60.00 2.849 0.134 3.1 03/02/09 39,807,886.7 281.3 1,840.02,942.3 283 60.00 2.870 0.135 2.8 03/02/09 39,564,187.0 280.0 1,840.02,924.3 281 60.00 2.617 0.122 3.1 03/02/09 37,488,155.8 278.0 1,840.02,770.9 260 60.00 2.364 0.105 3.3 03/02/09 37,387,939.0 278.8 1,840.02,743.1 259 60.00 2.637 0.116 3.8 03/02/09 38,435,510.3 279.4 1,840.02,778.3 267 60.00 2.849 0.127 3.6 03/02/09 39,142,131.7 279.2 1,840.02,850.6 274 60.00 3.256 0.148 3.7 03/02/09 39,889,090.9 281.2 1,840.02,926.6 279 60.00 3.062 0.143 3.9 03/02/09 40,279,396.8 282.0 1,840.02,955.3 282 60.00 3.147 0.149 3.8 03/02/09 40,244,086.9 282.2 1,840.02,974.6 283 60.00 3.293 0.157 3.2 03/02/09 40,161,131.6 280.7 1,840.02,968.4 283 60.00 3.208 0.152 3.5 03/02/09 40,420,226.5 280.51,840.02,921.7 283 60.00 2.762 0.129 3.6 03/02/09 40,733,208.4 281.51,840.02,944.3 285 60.00 3.021 0.142 3.1 03/02/09 41,174,881.9 281.2 1,840.02,998.6 288 60.00 3.085 0.148 2.2 03/02/09 39,914,162.8 278.7 1,840.02,950.2 283 60.00 2.617 0.123 1.9 03/02/09 33,226,824.3 269.7 1,840.02,419.8 227 60.00 1.885 0.073 2.9 03/02/09 30,372,230.1 272.3 1,840.02,178.9 209 60.00 1.653 0.058 03/02/09 36,264,994.7 277.51,840.02,621.3 251 60.00 2.504 0.105

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 0.5 0.7 03/05/09 24,900,973.7 266.0 1,840.0 1,705.2 161 60.00 0.456 0.012 0.7 03/05/09 24,199,573.1 264.7 1,840.0 1,657.2 159 60.00 0.638 0.017 0.6 03/05/09 24,428,264.2 264.9 1,840.0 1,686.1 162 60.00 0.633 0.017 0.6 03/05/09 24,549,556.6 265.7 1,840.0 1,681.1 161 60.00 0.547 0.015 0.7 03/05/09 25,279,945.9 266.51,840.0 1,731.1 165 60.00 0.547 0.015 1.2 03/04/09 25,434,175.4 266.2 1,840.0 1,727.9 164 60.00 0.643 0.018 1.6 03/04/09 26,621,732.5 268.51,840.0 1,837.5 179 60.00 1.085 0.032 1.7 03/04/09 32,114,164.9 271.6 1,840.02,234.0 215 60.00 1.435 0.051 1.8 03/04/09 31,056,292.2 270.7 1,840.02,143.5 208 60.00 1.537 0.053 1.8 03/04/09 31,801,490.8 273.4 1,840.02,195.0 214 60.00 1.627 0.057 1.7 03/04/09 34,118,299.9 274.6 1,840.02,429.1 229 60.00 1.578 0.061 1.5 03/04/09 28,642,512.1 269.0 1,840.0 1,992.6 189 60.00 1.525 0.049 1.8 03/04/09 26,820,114.6 267.51,840.0 1,880.3 175 60.00 1.335 0.040 1.1 03/04/09 26,445,693.6 266.3 1,840.0 1,882.8 178 60.00 1.578 0.047 1.2 03/04/09 24,800,776.5 266.8 1,840.0 1,752.2 163 60.00 0.972 0.027 1.3 03/04/09 26,934,655.2 270.2 1,840.0 1,903.0 183 60.00 1.060 0.032 1.6 03/04/09 32,282,872.6 273.3 1,840.02,298.4 218 60.00 1.139 0.042 2.3 03/04/09 32,466,760.2 273.0 1,840.02,311.5 220 60.00 1.402 0.052 3.4 03/04/09 33,006,270.0 274.8 1,840.02,385.8 230 60.00 1.986 0.076 3.5 03/04/09 35,971,186.6 277.8 1,840.02,639.2 251 60.00 2.892 0.122 2.6 03/04/09 39,887,085.0 281.1 1,840.02,948.2 280 60.00 2.955 0.139 1.9 03/04/09 39,247,332.5 278.2 1,840.02,879.5 272 60.00 2.211 0.102 2.0 03/04/09 33,254,558.4 271.3 1,840.02,385.7 223 60.00 1.653 0.063 1.4 03/04/09 26,673,190.1 264.1 1,840.0 1,899.0 175 60.00 1.753 0.053 1.6 03/04/09 24,365,734.4 264.4 1,840.0 1,695.0 160 60.00 1.256 0.034 1.5 03/04/09 24,890,248.8 265.51,840.0 1,731.5 163 60.00 1.435 0.040 1.9 03/04/09 24,591,723.2 265.51,840.0 1,697.4 159 60.00 1.356 0.037 1.8 03/04/09 24,347,036.3 264.8 1,840.0 1,680.5 158 60.00 1.718 0.046 12.5 03/04/09 24,424,503.0 267.0 1,840.0 1,685.9 167 60.00 1.627 0.044 2.3 03/03/09 27,559,394.6 268.0 1,840.0 1,962.1 189 60.00 10.956 0.344 3.1 03/03/09 32,132,749.4 275.3 1,840.02,322.7 224 60.00 1.986 0.074 3.3 03/03/09 36,846,084.9 279.8 1,840.02,723.4 257 60.00 2.617 0.114 3.1 03/03/09 40,186,528.7 282.1 1,840.02,970.3 282 60.00 2.786 0.132 3.0 03/03/09 40,359,841.5 281.6 1,840.02,961.2 283 60.00 2.637 0.125 2.4 03/03/09 39,963,081.5 280.8 1,840.02,953.8 283 60.00 2.533 0.120 2.5 03/03/09 37,942,364.1 277.1 1,840.02,804.4 265 60.00 2.026 0.091 03/03/09 37,886,451.6 278.51,840.02,800.3 265 60.00 2.111 0.095

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 C 02:00 C S S SC 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 0.9 1.1 03/06/09 32,943,736.7 271.0 1,840.02,345.5 216 60.00 0.789 0.030 1.3 03/06/09 32,616,122.8 271.8 1,840.02,251.2 214 60.00 0.994 0.036 2.4 03/06/09 32,978,672.9 272.2 1,840.02,276.3 218 60.00 1.175 0.043 1.9 03/06/09 33,335,910.0 272.3 1,840.02,355.3 224 60.00 2.120 0.080 1.8 03/06/09 32,782,667.7 269.2 1,840.02,280.6 210 60.00 1.704 0.062 1.8 03/06/09 30,674,834.3 271.1 1,840.02,150.6 207 60.00 1.602 0.055 1.8 03/06/09 33,416,329.6 272.2 1,840.02,379.1 222 60.00 1.578 0.060 1.7 03/06/09 29,975,099.1 269.51,840.02,101.5 197 60.00 1.602 0.054 1.6 03/06/09 33,269,531.4 274.2 1,840.02,350.6 226 60.00 1.501 0.056 1.2 03/06/09 36,736,392.9 274.2 1,840.02,575.5 248 60.00 1.424 0.059 0.7 03/06/09 35,429,260.9 271.7 1,840.02,503.1 237 60.00 1.060 0.042 0.4 03/06/09 29,348,023.9 265.7 1,840.02,089.5 194 60.00 0.614 0.020 0.4 03/06/09 25,273,154.3 263.8 1,840.0 1,716.9 161 60.00 0.367 0.010 0.4 03/06/09 25,206,979.7 264.1 1,840.0 1,685.0 158 60.00 0.373 0.010 12.5 03/06/09 24,530,703.3 263.7 1,840.0 1,653.2 153 60.00 0.370 0.010 0.6 03/06/09 24,062,118.5 262.7 1,840.0 1,608.5 153 60.00 11.668 0.300 0.6 03/06/09 24,342,283.7 263.4 1,840.0 1,640.4 156 60.00 0.556 0.015 12.5 03/06/09 25,015,935.1 264.4 1,840.0 1,685.9 159 60.00 0.556 0.015 0.8 03/05/09 25,088,841.2 265.1 1,840.0 1,677.1 159 60.00 11.668 0.313 2.0 03/05/09 25,879,368.0 267.8 1,840.0 1,758.1 166 60.00 0.735 0.021 2.0 03/05/09 30,606,443.1 270.9 1,840.02,145.7 205 60.00 1.780 0.061 2.2 03/05/09 34,063,864.8 274.3 1,840.02,388.2 232 60.00 1.780 0.068 2.1 03/05/09 37,248,704.9 278.2 1,840.02,611.5 254 60.00 1.958 0.082 2.0 03/05/09 38,871,137.7 276.2 1,840.02,746.3 263 60.00 1.855 0.081 2.3 03/05/09 31,669,469.2 270.6 1,840.02,220.3 210 60.00 1.780 0.063 2.3 03/05/09 31,424,418.2 271.3 1,840.02,203.1 212 60.00 2.047 0.072 2.0 03/05/09 33,146,158.8 273.51,840.02,323.8 222 60.00 2.047 0.076 2.1 03/05/09 34,257,289.3 276.51,840.02,401.7 232 60.00 1.780 0.068 2.0 03/05/09 36,507,693.4 277.4 1,840.02,599.2 251 60.00 1.841 0.076 1.8 03/05/09 37,442,530.3 278.7 1,840.02,665.8 256 60.00 1.753 0.075 2.3 03/05/09 36,061,368.4 277.51,840.02,567.4 244 60.00 1.578 0.065 2.3 03/05/09 37,220,501.1 279.2 1,840.02,670.2 254 60.00 2.001 0.085 2.0 03/05/09 38,703,739.4 280.51,840.02,797.6 267 60.00 1.986 0.089 1.8 03/05/09 38,395,576.3 279.51,840.02,754.5 264 60.00 1.740 0.077 1.2 03/05/09 37,539,073.4 276.7 1,840.02,652.2 256 60.00 1.590 0.067 0.7 03/05/09 32,892,710.8 272.3 1,840.02,306.1 219 60.00 1.068 0.039 03/05/09 29,814,022.0 269.0 1,840.02,090.2 198 60.00 0.623 0.021

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 0.7 0.5 03/08/09 26,821,991.3 263.4 1,840.0 1,822.1 175 60.00 0.643 0.019 0.6 03/08/09 24,344,863.7 261.3 1,840.0 1,680.3 157 60.00 0.452 0.012 0.5 03/08/09 23,526,615.6 262.2 1,840.0 1,636.7 151 60.00 0.538 0.014 0.3 03/08/09 23,390,258.3 262.8 1,840.0 1,652.6 149 60.00 0.442 0.012 12.5 03/08/09 23,361,411.9 263.6 1,840.0 1,599.7 148 60.00 0.273 0.007 12.5 03/08/09 24,482,097.9 263.3 1,840.0 1,729.7 159 60.00 11.040 0.305 12.5 03/08/09 23,896,633.3 263.1 1,840.0 1,701.4 157 60.00 10.956 0.298 0.2 03/07/09 23,864,145.8 264.2 1,840.0 1,686.0 154 60.00 11.040 0.298 0.4 03/07/09 24,055,981.3 265.51,840.0 1,673.5 154 60.00 0.179 0.005 0.8 03/07/09 28,579,245.7 271.0 1,840.02,003.6 191 60.00 0.356 0.011 1.5 03/07/09 32,661,589.8 275.0 1,840.02,378.6 223 60.00 0.685 0.026 1.1 03/07/09 36,231,210.1 275.9 1,840.02,697.6 251 60.00 1.257 0.054 0.7 03/07/09 38,036,030.1 277.8 1,840.02,790.7 263 60.00 0.936 0.042 0.5 03/07/09 36,219,327.3 275.1 1,840.02,598.3 244 60.00 0.609 0.025 0.2 03/07/09 33,644,085.0 272.8 1,840.02,395.3 222 60.00 0.438 0.017 0.4 03/07/09 30,530,223.3 270.9 1,840.02,223.4 205 60.00 0.171 0.006 0.5 03/07/09 29,471,718.5 269.9 1,840.02,194.4 201 60.00 0.335 0.012 0.6 03/07/09 32,299,732.5 270.7 1,840.02,299.6 217 60.00 0.438 0.016 1.3 03/07/09 33,400,478.1 272.7 1,840.02,359.8 222 60.00 0.530 0.020 2.1 03/07/09 34,465,928.3 274.2 1,840.02,435.1 229 60.00 1.148 0.045 1.5 03/07/09 33,759,401.0 272.9 1,840.02,403.5 222 60.00 1.841 0.071 1.1 03/07/09 33,153,839.5 272.2 1,840.02,342.4 216 60.00 1.325 0.050 0.7 03/07/09 28,862,021.4 267.0 1,840.02,023.5 182 60.00 0.979 0.032 1.2 03/07/09 24,881,824.4 265.51,840.0 1,758.0 158 60.00 0.618 0.017 1.2 03/07/09 24,096,770.6 263.7 1,840.0 1,689.4 155 60.00 1.068 0.029 1.1 03/07/09 24,107,559.0 264.2 1,840.0 1,690.2 156 60.00 1.068 0.029 0.7 03/07/09 23,471,247.0 264.51,840.0 1,645.5 149 60.00 0.979 0.026 0.7 03/07/09 23,622,653.4 264.51,840.0 1,643.3 149 60.00 0.628 0.016 1.0 03/07/09 23,444,980.9 263.9 1,840.0 1,631.0 149 60.00 0.628 0.016 0.8 03/07/09 22,973,941.3 263.51,840.0 1,635.6 149 60.00 0.876 0.023 0.6 03/07/09 23,032,303.7 263.7 1,840.0 1,652.3 150 60.00 0.696 0.018 0.7 03/06/09 23,848,719.8 265.2 1,840.0 1,672.0 152 60.00 0.534 0.014 1.7 03/06/09 24,907,714.8 266.6 1,840.0 1,746.3 161 60.00 0.623 0.017 1.9 03/06/09 28,199,488.5 270.4 1,840.0 1,961.7 186 60.00 1.525 0.048 1.9 03/06/09 33,831,497.9 274.4 1,840.02,408.6 230 60.00 1.665 0.064 1.5 03/06/09 36,177,916.8 275.2 1,840.02,575.7 246 60.00 1.665 0.069 03/06/09 37,748,467.3 275.7 1,840.02,667.0 256 60.00 1.325 0.056

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 0.6 0.6 03/09/09 37,607,105.0 278.7 1,840.02,759.2 257 60.00 0.510 0.023 0.4 03/09/09 39,865,431.1 280.2 1,840.02,946.5 280 60.00 0.507 0.024 0.7 03/09/09 39,083,803.9 277.7 1,840.02,931.3 274 60.00 0.333 0.016 0.8 03/09/09 36,479,457.2 275.8 1,840.02,696.3 251 60.00 0.591 0.025 0.7 03/09/09 36,070,896.6 276.0 1,840.02,646.5 246 60.00 0.680 0.029 0.7 03/09/09 35,790,288.9 274.4 1,840.02,625.9 244 60.00 0.595 0.025 1.1 03/09/09 36,755,801.5 277.7 1,840.02,696.8 253 60.00 0.595 0.026 1.2 03/09/09 39,028,016.4 279.51,840.02,927.1 272 60.00 0.915 0.043 1.2 03/09/09 39,944,691.2 280.7 1,840.03,017.6 282 60.00 0.991 0.048 1.1 03/09/09 38,984,470.6 278.9 1,840.02,966.2 278 60.00 0.984 0.047 1.1 03/09/09 39,427,185.3 279.51,840.02,999.9 281 60.00 0.902 0.043 0.9 03/09/09 39,689,927.7 278.9 1,840.03,019.9 283 60.00 0.902 0.044 0.8 03/09/09 39,157,735.1 277.4 1,840.02,979.4 277 60.00 0.738 0.035 0.7 03/09/09 37,941,157.6 278.0 1,840.02,866.2 266 60.00 0.661 0.030 0.4 03/09/09 36,119,405.5 272.0 1,840.02,708.9 243 60.00 0.582 0.025 0.3 03/09/09 30,719,389.5 268.8 1,840.02,203.8 204 60.00 0.348 0.012 0.2 03/09/09 28,550,667.8 265.2 1,840.02,048.2 187 60.00 0.261 0.009 0.1 03/09/09 26,257,562.5 264.3 1,840.0 1,855.2 169 60.00 0.177 0.005 0.1 03/09/09 24,707,921.5 263.8 1,840.0 1,745.7 158 60.00 0.088 0.002 0.2 03/09/09 24,227,248.4 264.2 1,840.0 1,711.7 154 60.00 0.088 0.002 0.7 03/08/09 24,405,512.9 264.0 1,840.0 1,724.3 156 60.00 0.177 0.005 0.9 03/08/09 26,307,566.4 267.2 1,840.0 1,844.4 175 60.00 0.623 0.018 0.9 03/08/09 33,664,021.3 272.4 1,840.02,396.7 230 60.00 0.789 0.030 0.8 03/08/09 35,573,517.7 275.2 1,840.02,552.0 242 60.00 0.783 0.032 0.5 03/08/09 38,178,625.4 277.9 1,840.02,801.2 263 60.00 0.680 0.030 0.4 03/08/09 36,644,206.0 272.51,840.02,648.7 245 60.00 0.432 0.018 0.5 03/08/09 28,918,355.8 265.51,840.02,058.8 193 60.00 0.351 0.012 0.6 03/08/09 26,687,322.8 262.51,840.0 1,871.0 171 60.00 0.445 0.013 0.7 03/08/09 27,511,028.1 266.1 1,840.0 1,913.8 184 60.00 0.538 0.016 0.7 03/08/09 33,702,078.3 272.0 1,840.02,381.1 229 60.00 0.618 0.024 0.8 03/08/09 34,745,106.1 272.3 1,840.02,473.7 232 60.00 0.614 0.024 0.4 03/08/09 36,377,415.9 276.1 1,840.02,570.1 244 60.00 0.707 0.029 0.3 03/08/09 36,573,158.8 272.9 1,840.02,603.8 243 60.00 0.351 0.015 0.5 03/08/09 30,076,735.4 268.3 1,840.02,125.0 197 60.00 0.265 0.009 0.4 03/08/09 28,135,384.5 265.8 1,840.0 1,972.5 185 60.00 0.445 0.014 0.4 03/08/09 28,229,129.4 264.7 1,840.0 1,979.1 185 60.00 0.356 0.011 03/08/09 24,261,444.5 262.4 1,840.0 1,648.2 158 60.00 0.367 0.010

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 S S S 14:00 S S SC 15:00 C 16:00 C 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 2.2 1.8 03/11/09 39,021,722.2 277.8 1,840.02,990.3 278 60.00 1.791 0.086 1.6 03/11/09 39,266,950.0 279.4 1,840.02,987.7 281 60.00 1.476 0.071 1.1 03/11/09 38,247,458.8 276.51,840.02,889.3 269 60.00 1.322 0.061 1.0 03/11/09 31,683,962.0 268.9 1,840.02,324.6 216 60.00 0.936 0.035 1.1 03/11/09 24,739,828.4 265.1 1,840.0 1,828.6 166 60.00 0.844 0.025 0.8 03/11/09 26,374,489.2 267.4 1,840.0 1,877.7 179 60.00 0.964 0.029 1.0 03/11/09 27,381,948.2 266.1 1,840.0 1,994.1 178 60.00 0.685 0.022 1.2 03/11/09 25,347,726.0 264.6 1,840.0 1,804.7 167 60.00 0.876 0.025 1.1 03/11/09 25,309,237.4 266.4 1,840.0 1,801.9 171 60.00 1.052 0.030 1.0 03/10/09 25,912,511.0 266.51,840.0 1,844.9 172 60.00 0.964 0.028 2.0 03/10/09 24,546,795.3 266.4 1,840.0 1,734.3 161 60.00 0.883 0.024 3.2 03/10/09 29,004,565.5 271.6 1,840.02,049.3 197 60.00 1.766 0.058 3.3 03/10/09 35,885,898.5 277.8 1,840.02,574.4 247 60.00 2.783 0.115 2.9 03/10/09 36,767,145.4 277.1 1,840.02,677.6 253 60.00 2.828 0.121 2.3 03/10/09 35,233,784.5 276.9 1,840.02,585.1 244 60.00 2.466 0.102 1.9 03/10/09 36,274,210.6 276.6 1,840.02,661.4 250 60.00 1.956 0.083 1.9 03/10/09 33,462,670.8 273.0 1,840.02,437.0 229 60.00 1.628 0.063 12.5 03/10/09 34,970,725.1 276.0 1,840.02,546.8 239 60.00 1.628 0.066 12.5 03/10/09 36,175,556.9 275.3 1,840.02,634.6 246 60.00 10.710 0.451 1.4 03/10/09 35,406,327.1 276.8 1,840.02,578.5 243 60.00 10.710 0.442 0.9 03/10/09 37,291,433.1 278.0 1,840.02,736.0 259 60.00 1.191 0.052 0.7 03/10/09 38,696,579.1 279.2 1,840.02,860.2 271 60.00 0.760 0.035 1.0 03/10/09 37,012,796.9 278.51,840.02,735.7 256 60.00 0.591 0.026 1.1 03/10/09 39,640,730.6 282.0 1,840.02,994.6 280 60.00 0.826 0.040 1.1 03/10/09 40,330,061.7 281.3 1,840.03,002.8 282 60.00 0.922 0.044 0.6 03/10/09 38,828,661.7 279.6 1,840.02,933.3 272 60.00 0.909 0.043 0.3 03/10/09 36,691,648.7 275.3 1,840.02,751.9 253 60.00 0.499 0.022 0.2 03/10/09 32,062,390.8 267.9 1,840.02,247.8 206 60.00 0.267 0.010 0.3 03/10/09 24,885,888.6 265.2 1,840.0 1,771.8 160 60.00 0.175 0.005 0.2 03/10/09 25,013,012.9 263.9 1,840.0 1,780.8 160 60.00 0.263 0.007 0.2 03/10/09 24,171,684.8 262.6 1,840.0 1,681.5 154 60.00 0.179 0.005 0.2 03/10/09 24,090,947.2 264.2 1,840.0 1,702.1 156 60.00 0.177 0.005 12.5 03/10/09 24,488,418.8 263.9 1,840.0 1,716.8 157 60.00 0.178 0.005 0.5 03/09/09 24,609,091.8 265.6 1,840.0 1,725.3 159 60.00 11.126 0.307 0.5 03/09/09 28,876,084.9 271.51,840.02,071.5 199 60.00 0.435 0.014 0.7 03/09/09 34,607,094.0 275.6 1,840.02,557.9 238 60.00 0.422 0.017 03/09/09 35,513,153.2 277.0 1,840.02,586.3 243 60.00 0.600 0.025

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 1.3 1.5 03/12/09 35,258,064.8 276.1 1,840.02,721.0 250 60.00 1.051 0.046 1.6 03/12/09 36,644,945.9 276.0 1,840.02,828.0 258 60.00 1.213 0.055 1.4 03/12/09 36,192,458.9 274.51,840.02,793.1 258 60.00 1.294 0.058 1.1 03/12/09 36,756,645.0 276.6 1,840.02,856.7 264 60.00 1.124 0.051 1.1 03/12/09 39,420,763.4 279.0 1,840.03,128.0 283 60.00 0.865 0.043 1.1 03/12/09 39,407,949.8 278.8 1,840.03,062.7 283 60.00 0.883 0.043 1.0 03/12/09 39,526,186.8 280.0 1,840.03,071.9 282 60.00 0.883 0.043 1.0 03/12/09 39,616,522.7 278.3 1,840.03,057.4 282 60.00 0.809 0.040 1.0 03/12/09 39,713,560.2 278.51,840.03,064.9 282 60.00 0.809 0.040 1.0 03/12/09 39,425,392.1 277.9 1,840.03,064.0 282 60.00 0.803 0.039 1.4 03/12/09 39,330,985.9 278.4 1,840.03,078.1 282 60.00 0.797 0.039 2.2 03/12/09 39,303,241.3 278.51,840.03,075.9 281 60.00 1.116 0.055 2.5 03/12/09 39,667,050.5 279.6 1,840.03,104.4 281 60.00 1.754 0.087 2.6 03/12/09 39,395,547.7 278.7 1,840.03,104.6 283 60.00 1.980 0.098 2.7 03/12/09 39,468,240.5 278.3 1,840.03,045.9 283 60.00 2.102 0.102 2.3 03/12/09 39,394,506.8 277.2 1,840.03,018.9 282 60.00 2.199 0.106 1.9 03/12/09 36,031,589.0 269.51,840.02,682.8 247 60.00 1.928 0.083 2.0 03/12/09 29,995,991.3 266.6 1,840.02,184.5 206 60.00 1.628 0.057 2.5 03/12/09 31,636,402.6 271.51,840.02,321.1 220 60.00 1.701 0.063 2.5 03/12/09 34,680,441.4 270.7 1,840.02,525.6 236 60.00 2.142 0.087 2.8 03/12/09 33,145,120.9 272.4 1,840.02,449.8 231 60.00 2.111 0.083 12.5 03/12/09 36,240,418.4 272.8 1,840.02,757.4 254 60.00 2.296 0.101 2.9 03/11/09 35,323,981.2 272.8 1,840.02,630.1 246 60.00 10.476 0.441 3.1 03/11/09 37,486,601.2 274.7 1,840.02,791.2 262 60.00 2.430 0.108 3.2 03/11/09 39,045,305.5 276.4 1,840.02,885.9 273 60.00 2.617 0.121 3.2 03/11/09 39,166,644.8 277.7 1,840.02,916.2 273 60.00 2.682 0.125 3.1 03/11/09 39,942,503.4 278.9 1,840.02,995.7 279 60.00 2.662 0.128 2.9 03/11/09 40,187,768.8 277.7 1,840.03,014.1 282 60.00 2.579 0.124 2.7 03/11/09 39,099,673.0 277.2 1,840.02,953.8 271 60.00 2.395 0.113 2.7 03/11/09 37,803,528.4 275.0 1,840.02,855.8 264 60.00 2.230 0.102 2.8 03/11/09 35,654,740.9 273.2 1,840.02,674.1 250 60.00 2.246 0.096 2.5 03/11/09 36,572,467.2 274.2 1,840.02,762.8 257 60.00 2.313 0.102 2.1 03/11/09 36,675,376.7 274.9 1,840.02,770.6 257 60.00 2.065 0.091 2.4 03/11/09 37,286,160.8 277.2 1,840.02,837.0 262 60.00 1.722 0.078 2.5 03/11/09 38,918,179.8 278.3 1,840.03,003.5 278 60.00 1.941 0.093 2.3 03/11/09 39,070,738.3 278.4 1,840.03,015.3 280 60.00 2.021 0.097 03/11/09 39,322,590.8 278.1 1,840.02,992.0 282 60.00 1.886 0.090

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 23:00 00:00 01:00 C 02:00 C S S SC 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 0.5 0.6 03/14/09 25,865,142.5 266.7 1,840.0 1,827.4 181 60.00 0.442 0.013 0.6 03/14/09 29,739,228.1 268.8 1,840.02,198.1 211 60.00 0.507 0.018 0.7 03/14/09 30,665,905.6 269.8 1,840.02,266.6 217 60.00 0.507 0.018 1.0 03/14/09 32,589,668.6 273.9 1,840.02,408.8 230 60.00 0.591 0.023 1.1 03/14/09 36,185,925.3 273.7 1,840.02,753.3 255 60.00 0.820 0.036 0.9 03/14/09 28,085,772.6 263.51,840.02,060.7 190 60.00 0.936 0.031 0.7 03/14/09 24,327,020.5 263.6 1,840.0 1,745.2 164 60.00 0.783 0.022 0.7 03/14/09 24,486,654.2 264.0 1,840.0 1,756.7 164 60.00 0.609 0.017 12.5 03/14/09 24,579,996.7 264.2 1,840.0 1,750.0 164 60.00 0.614 0.017 12.5 03/14/09 24,230,193.8 263.6 1,840.0 1,751.4 164 60.00 10.791 0.302 12.5 03/14/09 24,367,231.3 263.7 1,840.0 1,761.3 164 60.00 10.791 0.304 0.9 03/13/09 24,338,681.8 263.8 1,840.0 1,759.3 164 60.00 10.791 0.304 0.8 03/13/09 25,788,744.9 265.51,840.0 1,892.1 179 60.00 0.765 0.023 1.3 03/13/09 27,040,303.2 269.2 1,840.02,013.3 193 60.00 0.670 0.022 1.9 03/13/09 35,783,317.6 278.1 1,840.02,722.6 259 60.00 1.066 0.046 2.3 03/13/09 39,037,629.5 280.2 1,840.02,991.5 283 60.00 1.547 0.074 1.9 03/13/09 39,151,665.6 278.6 1,840.03,000.2 278 60.00 1.873 0.090 1.5 03/13/09 33,622,590.2 269.6 1,840.02,521.7 232 60.00 1.581 0.064 1.6 03/13/09 28,253,426.6 267.3 1,840.02,088.3 194 60.00 1.266 0.042 1.8 03/13/09 27,949,377.2 267.9 1,840.02,065.8 193 60.00 1.351 0.045 2.4 03/13/09 30,881,823.1 275.8 1,840.02,299.4 217 60.00 1.509 0.055 2.2 03/13/09 39,878,976.4 280.6 1,840.03,077.6 283 60.00 1.941 0.095 2.2 03/13/09 39,503,529.9 280.1 1,840.03,027.2 283 60.00 1.791 0.087 2.0 03/13/09 39,585,099.3 279.51,840.03,033.4 282 60.00 1.791 0.087 1.7 03/13/09 39,467,841.3 278.4 1,840.02,960.1 281 60.00 1.664 0.079 1.4 03/13/09 39,399,574.0 277.7 1,840.02,997.8 283 60.00 1.394 0.067 1.5 03/13/09 39,619,896.8 278.6 1,840.03,014.6 283 60.00 1.148 0.055 1.0 03/13/09 39,867,746.3 277.9 1,840.02,968.4 282 60.00 1.257 0.060 0.8 03/13/09 35,031,494.6 270.3 1,840.02,646.4 244 60.00 0.826 0.035 0.9 03/13/09 27,302,143.1 265.7 1,840.02,092.2 194 60.00 0.651 0.022 1.0 03/13/09 27,274,456.9 265.4 1,840.02,045.6 193 60.00 0.749 0.024 12.5 03/13/09 27,580,278.2 266.9 1,840.02,083.5 193 60.00 0.826 0.028 1.7 03/13/09 27,666,021.9 267.3 1,840.02,075.0 193 60.00 10.400 0.345 1.5 03/13/09 27,908,511.1 267.4 1,840.02,108.3 194 60.00 1.404 0.047 1.3 03/13/09 27,228,331.6 266.4 1,840.02,086.5 193 60.00 1.221 0.041 1.4 03/12/09 27,174,676.6 266.1 1,840.02,082.4 193 60.00 1.059 0.035 03/12/09 27,237,816.4 269.2 1,840.02,072.5 194 60.00 1.148 0.038

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 6.1 0.5 03/15/09 23,044,789.6 263.51,840.0 1,665.8 155 60.00 5.266 0.140 0.5 03/15/09 23,832,796.7 263.51,840.0 1,709.8 159 60.00 0.435 0.012 0.6 03/15/09 23,252,574.0 263.51,840.0 1,668.2 154 60.00 0.435 0.012 0.8 03/15/09 24,269,587.4 266.6 1,840.0 1,767.5 169 60.00 0.514 0.015 1.0 03/15/09 29,824,423.2 272.2 1,840.02,220.6 214 60.00 0.670 0.024 0.9 03/15/09 33,244,539.4 274.1 1,840.02,511.4 235 60.00 0.826 0.033 0.7 03/15/09 30,661,864.0 267.4 1,840.02,299.7 213 60.00 0.749 0.028 0.7 03/15/09 25,068,825.0 264.1 1,840.0 1,812.1 170 60.00 0.604 0.018 0.5 03/15/09 25,383,371.6 264.2 1,840.0 1,834.7 173 60.00 0.604 0.018 0.4 03/15/09 23,759,589.2 263.7 1,840.0 1,691.6 158 60.00 0.438 0.012 1.0 03/15/09 24,590,495.2 264.3 1,840.0 1,750.7 163 60.00 0.351 0.010 1.5 03/15/09 23,994,633.1 263.3 1,840.0 1,734.4 159 60.00 0.863 0.024 0.9 03/15/09 24,747,494.9 264.51,840.0 1,775.3 167 60.00 1.305 0.037 0.7 03/15/09 28,183,407.6 267.6 1,840.02,037.1 195 60.00 0.777 0.025 0.7 03/15/09 28,339,129.7 267.1 1,840.02,033.0 196 60.00 0.609 0.020 0.4 03/15/09 29,024,552.8 267.3 1,840.02,082.2 199 60.00 0.609 0.020 0.3 03/15/09 26,028,509.2 263.6 1,840.0 1,867.3 174 60.00 0.348 0.010 0.3 03/15/09 23,923,754.1 263.6 1,840.0 1,716.3 162 60.00 0.261 0.007 0.4 03/15/09 24,504,481.6 263.6 1,840.0 1,744.6 164 60.00 0.263 0.007 0.5 03/15/09 24,375,231.3 264.0 1,840.0 1,735.4 165 60.00 0.351 0.010 0.5 03/15/09 24,270,320.7 263.2 1,840.0 1,780.7 160 60.00 0.425 0.012 0.8 03/15/09 22,734,828.8 262.3 1,840.0 1,655.7 152 60.00 0.428 0.011 0.7 03/15/09 22,397,163.6 262.7 1,840.0 1,655.4 153 60.00 0.675 0.018 1.1 03/15/09 24,030,000.5 264.1 1,840.0 1,750.0 163 60.00 0.600 0.017 0.6 03/14/09 23,141,555.6 262.7 1,840.0 1,685.3 155 60.00 0.943 0.025 0.4 03/14/09 23,161,565.5 262.8 1,840.0 1,686.8 156 60.00 0.514 0.014 0.6 03/14/09 22,778,372.0 262.7 1,840.0 1,658.8 154 60.00 0.343 0.009 1.6 03/14/09 26,156,613.1 267.3 1,840.0 1,862.3 183 60.00 0.526 0.016 1.3 03/14/09 32,402,231.7 272.9 1,840.02,359.7 227 60.00 1.371 0.052 1.0 03/14/09 31,993,534.0 268.7 1,840.02,364.8 224 60.00 1.098 0.042 0.9 03/14/09 26,366,116.9 263.6 1,840.0 1,862.8 178 60.00 0.883 0.026 0.9 03/14/09 24,790,936.4 264.2 1,840.0 1,738.1 170 60.00 0.801 0.022 0.8 03/14/09 25,433,030.6 262.8 1,840.0 1,852.2 176 60.00 0.771 0.023 0.7 03/14/09 22,854,194.5 262.1 1,840.0 1,639.5 155 60.00 0.696 0.018 0.6 03/14/09 23,423,789.9 262.51,840.0 1,693.1 159 60.00 0.604 0.016 0.5 03/14/09 23,985,293.8 263.7 1,840.0 1,733.7 164 60.00 0.518 0.014 03/14/09 24,582,613.5 263.4 1,840.0 1,790.3 169 60.00 0.428 0.012

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 0.6 0.5 03/17/09 30,621,843.4 272.6 1,840.02,246.7 211 60.00 0.510 0.018 1.4 03/17/09 28,510,317.1 273.1 1,840.02,060.8 197 60.00 0.432 0.014 1.4 03/17/09 35,000,546.7 280.2 1,840.02,606.1 246 60.00 1.173 0.049 1.1 03/17/09 34,554,310.0 277.2 1,840.02,610.3 240 60.00 1.156 0.048 0.8 03/17/09 33,054,606.0 275.0 1,840.02,479.1 230 60.00 0.915 0.036 1.1 03/17/09 30,329,358.0 271.0 1,840.02,241.7 212 60.00 0.675 0.024 0.8 03/17/09 30,852,343.4 273.4 1,840.02,280.4 217 60.00 0.929 0.034 0.5 03/17/09 30,605,571.6 270.0 1,840.02,262.2 213 60.00 0.675 0.024 0.5 03/17/09 26,350,799.8 266.6 1,840.0 1,904.7 177 60.00 0.432 0.013 0.5 03/17/09 24,388,782.9 266.4 1,840.0 1,723.1 159 60.00 0.442 0.012 0.7 03/17/09 24,097,105.1 265.6 1,840.0 1,702.5 156 60.00 0.442 0.012 0.7 03/17/09 23,013,321.6 264.51,840.0 1,675.9 153 60.00 0.600 0.016 0.7 03/17/09 22,720,952.1 264.51,840.0 1,654.7 152 60.00 0.600 0.016 0.6 03/16/09 23,122,132.4 264.9 1,840.0 1,709.0 155 60.00 0.591 0.016 0.5 03/16/09 23,232,569.6 264.3 1,840.0 1,704.6 156 60.00 0.510 0.014 0.8 03/16/09 24,175,310.9 266.4 1,840.0 1,721.2 163 60.00 0.438 0.012 1.2 03/16/09 27,147,972.7 271.0 1,840.0 1,977.1 188 60.00 0.685 0.022 1.3 03/16/09 32,033,042.1 275.51,840.02,350.2 224 60.00 1.021 0.038 1.1 03/16/09 33,312,046.4 273.4 1,840.02,462.2 230 60.00 1.098 0.043 0.7 03/16/09 27,279,198.3 267.8 1,840.02,001.4 185 60.00 0.936 0.030 0.4 03/16/09 25,795,996.8 267.0 1,840.0 1,906.7 175 60.00 0.591 0.018 0.7 03/16/09 26,124,522.1 269.7 1,840.0 1,931.0 179 60.00 0.338 0.010 1.3 03/16/09 27,611,779.9 270.3 1,840.02,040.9 190 60.00 0.591 0.019 1.6 03/16/09 31,216,963.6 274.2 1,840.02,273.4 219 60.00 1.114 0.040 1.7 03/16/09 34,639,613.9 278.4 1,840.02,579.2 245 60.00 1.341 0.055 1.6 03/16/09 37,556,613.1 283.7 1,840.02,857.6 265 60.00 1.394 0.064 1.4 03/16/09 38,077,688.0 282.7 1,840.02,897.2 271 60.00 1.312 0.061 1.2 03/16/09 36,668,595.6 280.6 1,840.02,770.1 260 60.00 1.156 0.051 1.3 03/16/09 34,634,358.1 277.3 1,840.02,578.7 248 60.00 1.006 0.041 1.2 03/16/09 35,046,218.1 278.1 1,840.02,609.4 251 60.00 1.089 0.045 1.1 03/16/09 34,976,898.2 277.51,840.02,623.3 251 60.00 0.998 0.042 0.7 03/16/09 34,315,548.0 274.51,840.02,573.7 244 60.00 0.915 0.038 0.6 03/16/09 31,139,967.1 269.3 1,840.02,318.6 218 60.00 0.587 0.022 0.5 03/16/09 25,090,643.1 264.7 1,840.0 1,827.3 170 60.00 0.514 0.015 0.7 03/16/09 23,337,368.2 264.3 1,840.0 1,674.2 155 60.00 0.435 0.012 0.8 03/16/09 23,038,064.4 263.6 1,840.0 1,677.8 153 60.00 0.600 0.016 03/16/09 22,719,076.1 262.3 1,840.0 1,666.9 153 60.00 0.680 0.018

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 0.5 0.4 03/19/09 23,525,813.1 263.2 1,840.0 1,674.9 159 60.00 0.438 0.012 0.4 03/19/09 23,668,027.2 264.1 1,840.0 1,672.2 159 60.00 0.353 0.009 0.9 03/18/09 24,436,907.1 266.1 1,840.0 1,739.8 163 60.00 0.351 0.010 0.9 03/18/09 25,155,628.2 268.0 1,840.0 1,845.7 174 60.00 0.765 0.023 0.8 03/18/09 28,009,290.8 267.1 1,840.02,070.2 193 60.00 0.760 0.025 1.5 03/18/09 26,218,948.9 270.0 1,840.0 1,880.9 182 60.00 0.696 0.021 1.4 03/18/09 32,530,156.2 277.0 1,840.02,386.7 230 60.00 1.276 0.049 0.6 03/18/09 37,781,999.8 279.9 1,840.02,833.7 264 60.00 1.165 0.053 0.8 03/18/09 31,969,549.6 270.51,840.02,345.6 220 60.00 0.510 0.019 0.7 03/18/09 26,746,722.1 266.9 1,840.0 1,947.9 186 60.00 0.685 0.021 1.2 03/18/09 25,162,653.0 266.0 1,840.0 1,832.5 171 60.00 0.600 0.018 1.5 03/18/09 26,457,309.6 267.9 1,840.0 1,811.7 177 60.00 1.093 0.032 1.9 03/18/09 31,861,820.6 271.7 1,840.02,147.2 207 60.00 1.389 0.048 2.1 03/18/09 35,995,147.1 277.0 1,840.02,543.1 241 60.00 1.678 0.068 2.2 03/18/09 35,929,585.9 278.51,840.02,616.6 243 60.00 1.799 0.075 2.0 03/18/09 39,099,925.1 281.6 1,840.02,868.8 270 60.00 1.871 0.086 2.0 03/18/09 38,206,552.5 279.9 1,840.02,824.0 263 60.00 1.688 0.076 1.4 03/18/09 35,967,304.6 277.4 1,840.02,638.9 250 60.00 1.701 0.072 1.0 03/18/09 33,078,439.3 275.3 1,840.02,444.9 233 60.00 1.182 0.046 0.4 03/18/09 34,783,892.2 275.6 1,840.02,627.7 243 60.00 0.826 0.035 0.3 03/18/09 30,387,760.7 269.0 1,840.02,213.0 205 60.00 0.343 0.012 0.5 03/18/09 25,437,447.6 264.51,840.0 1,783.4 165 60.00 0.267 0.008 0.4 03/18/09 24,260,152.6 263.3 1,840.0 1,714.0 161 60.00 0.442 0.012 0.3 03/18/09 23,779,157.0 263.8 1,840.0 1,654.2 159 60.00 0.359 0.009 0.3 03/18/09 23,976,807.1 263.51,840.0 1,668.0 157 60.00 0.269 0.007 3.9 03/18/09 24,603,073.4 263.51,840.0 1,671.4 157 60.00 0.276 0.007 0.0 03/17/09 23,705,006.1 263.9 1,840.0 1,649.0 155 60.00 3.498 0.092 0.0 03/17/09 23,883,671.9 264.51,840.0 1,674.5 155 60.00 0.000 0.000 0.2 03/17/09 24,147,220.5 264.8 1,840.0 1,706.0 156 60.00 0.000 0.000 0.6 03/17/09 24,810,912.5 268.0 1,840.0 1,753.0 173 60.00 0.177 0.005 0.5 03/17/09 32,490,269.0 276.4 1,840.02,383.8 228 60.00 0.510 0.019 0.3 03/17/09 33,550,979.0 273.0 1,840.02,443.4 225 60.00 0.428 0.017 0.4 03/17/09 27,716,580.8 268.3 1,840.0 1,943.2 182 60.00 0.267 0.008 0.7 03/17/09 24,539,789.8 265.51,840.0 1,760.5 161 60.00 0.348 0.010 0.6 03/17/09 24,025,653.0 266.6 1,840.0 1,723.6 161 60.00 0.609 0.017 0.6 03/17/09 24,653,844.2 266.1 1,840.0 1,795.5 165 60.00 0.514 0.015 03/17/09 26,022,157.5 270.8 1,840.0 1,852.7 180 60.00 0.526 0.016

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 S S SC 02:00 C S S SC 03:00 S S SC 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 0.6 1.3 03/20/09 25,177,373.3 265.6 1,840.0 1,819.9 169 60.00 0.518 0.015 1.9 03/20/09 25,926,709.9 267.8 1,840.0 1,860.0 177 60.00 1.131 0.034 2.2 03/20/09 28,146,588.5 270.7 1,840.02,019.2 196 60.00 1.653 0.053 2.0 03/20/09 34,564,595.7 276.51,840.02,611.2 241 60.00 1.817 0.076 1.8 03/20/09 36,856,927.4 277.7 1,840.02,764.3 256 60.00 1.664 0.074 2.4 03/20/09 35,556,701.5 276.0 1,840.02,647.5 246 60.00 1.509 0.064 2.3 03/20/09 35,953,705.7 277.7 1,840.02,696.6 248 60.00 1.997 0.086 1.8 03/20/09 37,540,191.9 278.1 1,840.02,713.5 254 60.00 1.986 0.086 1.4 03/20/09 35,733,683.9 276.9 1,840.02,602.4 242 60.00 1.542 0.064 1.0 03/20/09 34,918,088.6 272.2 1,840.02,486.0 232 60.00 1.227 0.049 3.9 03/20/09 27,527,378.6 264.8 1,840.0 1,914.9 181 60.00 0.897 0.027 3.9 03/20/09 25,838,604.8 265.6 1,840.0 1,769.4 172 60.00 3.554 0.101 3.9 03/20/09 24,373,621.2 263.8 1,840.0 1,669.1 155 60.00 3.554 0.095 3.9 03/20/09 24,035,856.8 263.0 1,840.0 1,659.0 152 60.00 3.526 0.094 3.9 03/20/09 22,778,667.2 264.1 1,840.0 1,609.4 152 60.00 3.444 0.089 2.1 03/19/09 27,961,786.6 269.8 1,840.0 1,945.2 193 60.00 3.498 0.109 2.1 03/19/09 33,964,032.9 273.51,840.02,344.3 226 60.00 1.899 0.071 2.7 03/19/09 35,404,268.5 274.2 1,840.02,482.1 235 60.00 1.869 0.074 2.6 03/19/09 36,190,663.1 276.7 1,840.02,576.6 245 60.00 2.366 0.098 2.4 03/19/09 37,696,102.3 279.6 1,840.02,806.7 266 60.00 2.179 0.098 2.1 03/19/09 38,590,760.3 278.3 1,840.02,873.4 274 60.00 2.011 0.092 2.1 03/19/09 35,105,862.7 274.3 1,840.02,594.8 245 60.00 1.773 0.074 1.9 03/19/09 34,330,018.1 272.8 1,840.02,556.1 239 60.00 1.760 0.072 1.6 03/19/09 33,037,299.5 271.51,840.02,477.8 229 60.00 1.581 0.063 1.4 03/19/09 30,975,003.6 271.0 1,840.02,306.3 215 60.00 1.341 0.049 2.1 03/19/09 31,704,606.7 272.9 1,840.02,377.9 224 60.00 1.165 0.044 1.8 03/19/09 35,388,214.9 276.3 1,840.02,615.6 248 60.00 1.773 0.074 1.6 03/19/09 36,427,256.1 277.2 1,840.02,751.8 257 60.00 1.487 0.065 1.4 03/19/09 34,767,338.8 275.7 1,840.02,607.5 245 60.00 1.331 0.056 2.5 03/19/09 34,954,852.5 275.6 1,840.02,621.6 246 60.00 1.165 0.049 2.8 03/19/09 35,312,673.1 277.6 1,840.02,667.7 252 60.00 2.065 0.088 2.2 03/19/09 38,352,652.7 278.7 1,840.02,918.2 277 60.00 2.296 0.107 1.3 03/19/09 38,735,499.9 278.0 1,840.02,947.2 276 60.00 1.804 0.085 0.7 03/19/09 33,890,145.2 272.9 1,840.02,541.8 234 60.00 1.082 0.044 0.8 03/19/09 29,853,327.3 267.51,840.02,190.3 204 60.00 0.595 0.021 0.6 03/19/09 25,504,570.1 263.4 1,840.0 1,857.4 173 60.00 0.685 0.020 03/19/09 23,917,454.1 262.6 1,840.0 1,702.8 161 60.00 0.526 0.014

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 0.4 0.3 03/22/09 24,037,636.7 263.0 1,840.0 1,659.1 155 60.00 0.362 0.010 0.6 03/22/09 23,758,025.5 263.3 1,840.0 1,639.8 152 60.00 0.271 0.007 0.7 03/22/09 23,168,698.6 262.9 1,840.0 1,624.3 152 60.00 0.534 0.014 3.9 03/22/09 23,766,528.4 263.4 1,840.0 1,705.0 158 60.00 0.609 0.017 0.1 03/21/09 23,717,156.1 262.51,840.0 1,701.4 156 60.00 3.392 0.092 0.5 03/21/09 23,098,124.0 263.3 1,840.0 1,657.0 153 60.00 0.087 0.002 1.0 03/21/09 25,773,534.2 268.6 1,840.0 1,821.0 177 60.00 0.442 0.013 1.7 03/21/09 32,800,458.3 274.51,840.02,406.5 226 60.00 0.850 0.033 2.4 03/21/09 35,262,131.3 277.3 1,840.02,625.5 244 60.00 1.425 0.060 2.0 03/21/09 37,157,540.5 277.8 1,840.02,766.7 257 60.00 2.011 0.089 1.8 03/21/09 33,862,961.0 272.8 1,840.02,484.5 230 60.00 1.701 0.068 1.6 03/21/09 30,850,264.9 270.8 1,840.02,246.7 210 60.00 1.542 0.055 1.1 03/21/09 31,697,906.1 270.9 1,840.02,325.7 220 60.00 1.361 0.051 1.1 03/21/09 28,771,054.6 268.1 1,840.02,079.6 195 60.00 0.950 0.032 1.2 03/21/09 29,211,966.3 268.9 1,840.02,111.5 198 60.00 0.950 0.032 1.5 03/21/09 29,569,442.7 269.51,840.02,153.4 203 60.00 1.028 0.035 1.8 03/21/09 30,367,858.0 271.3 1,840.02,228.1 214 60.00 1.276 0.045 2.0 03/21/09 33,738,753.1 276.0 1,840.02,512.1 236 60.00 1.509 0.061 1.7 03/21/09 36,979,966.6 279.1 1,840.02,793.6 257 60.00 1.652 0.074 1.1 03/21/09 37,327,382.5 278.2 1,840.02,799.5 257 60.00 1.414 0.063 1.0 03/21/09 32,707,809.3 270.6 1,840.02,382.0 223 60.00 0.943 0.036 1.0 03/21/09 27,961,406.4 268.0 1,840.02,005.9 193 60.00 0.870 0.028 0.7 03/21/09 27,946,153.2 265.4 1,840.0 1,974.4 187 60.00 0.883 0.028 0.6 03/21/09 23,785,456.8 262.7 1,840.0 1,680.5 156 60.00 0.618 0.017 0.5 03/21/09 23,899,019.2 264.9 1,840.0 1,675.5 159 60.00 0.534 0.014 0.5 03/21/09 24,897,227.1 264.4 1,840.0 1,759.0 164 60.00 0.442 0.012 0.6 03/21/09 23,789,046.8 263.8 1,840.0 1,680.7 154 60.00 0.442 0.012 0.7 03/21/09 23,521,808.7 263.7 1,840.0 1,661.9 156 60.00 0.530 0.014 0.7 03/20/09 23,934,904.0 264.3 1,840.0 1,691.1 158 60.00 0.618 0.017 1.0 03/20/09 23,989,431.0 265.1 1,840.0 1,707.9 157 60.00 0.614 0.017 1.1 03/20/09 27,631,884.2 268.9 1,840.0 1,937.2 188 60.00 0.890 0.028 1.6 03/20/09 30,222,380.1 270.8 1,840.02,151.7 209 60.00 0.964 0.033 1.4 03/20/09 32,437,229.2 275.1 1,840.02,397.5 229 60.00 1.351 0.052 0.6 03/20/09 34,313,094.3 271.7 1,840.02,573.5 237 60.00 1.165 0.048 0.6 03/20/09 25,489,636.8 263.2 1,840.0 1,870.2 169 60.00 0.510 0.015 0.7 03/20/09 22,910,532.0 262.7 1,840.0 1,643.6 152 60.00 0.522 0.014 03/20/09 24,436,678.0 266.0 1,840.0 1,766.4 166 60.00 0.604 0.017

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 0.8 0.4 03/23/09 26,857,120.7 262.9 1,840.0 1,853.7 177 60.00 0.723 0.021 0.0 03/23/09 23,619,081.1 263.2 1,840.0 1,643.1 154 60.00 0.359 0.009 0.2 03/23/09 25,657,676.2 265.4 1,840.0 1,840.7 176 60.00 0.000 0.000 0.3 03/23/09 28,069,013.3 268.0 1,840.0 1,998.4 195 60.00 0.175 0.006 0.3 03/23/09 33,820,656.1 272.2 1,840.02,389.5 230 60.00 0.265 0.010 0.4 03/23/09 36,008,826.4 275.6 1,840.02,583.3 247 60.00 0.261 0.011 0.5 03/23/09 39,395,283.5 277.8 1,840.02,826.2 270 60.00 0.348 0.016 1.4 03/23/09 38,466,746.3 276.8 1,840.02,780.5 267 60.00 0.432 0.019 1.1 03/23/09 36,753,301.4 278.51,840.02,736.5 260 60.00 1.173 0.051 0.3 03/23/09 39,197,368.2 279.9 1,840.02,961.1 275 60.00 0.909 0.043 0.4 03/23/09 35,567,948.4 271.8 1,840.02,570.9 242 60.00 0.259 0.011 1.0 03/23/09 25,692,670.6 263.6 1,840.0 1,815.3 173 60.00 0.353 0.010 0.4 03/23/09 24,210,276.5 262.8 1,840.0 1,710.5 164 60.00 0.883 0.024 0.3 03/23/09 24,579,815.2 263.8 1,840.0 1,736.6 162 60.00 0.353 0.010 0.2 03/23/09 24,300,343.1 264.0 1,840.0 1,703.6 162 60.00 0.267 0.007 0.4 03/23/09 24,210,150.8 263.9 1,840.0 1,710.5 159 60.00 0.177 0.005 0.2 03/23/09 23,466,718.6 262.9 1,840.0 1,696.3 157 60.00 0.345 0.009 0.1 03/22/09 23,345,178.0 263.8 1,840.0 1,687.4 155 60.00 0.173 0.005 0.6 03/22/09 23,853,411.4 264.51,840.0 1,711.2 159 60.00 0.087 0.002 1.2 03/22/09 26,214,332.2 267.9 1,840.0 1,894.8 179 60.00 0.518 0.016 1.2 03/22/09 30,521,962.4 270.0 1,840.02,239.4 211 60.00 1.021 0.037 0.9 03/22/09 32,168,464.7 273.2 1,840.02,360.2 228 60.00 1.021 0.039 0.4 03/22/09 36,992,479.0 273.8 1,840.02,754.3 255 60.00 0.754 0.033 0.4 03/22/09 29,533,250.7 266.3 1,840.02,118.7 199 60.00 0.348 0.012 0.7 03/22/09 24,736,465.9 264.0 1,840.0 1,720.8 164 60.00 0.359 0.010 0.9 03/22/09 25,801,307.2 264.7 1,840.0 1,836.9 176 60.00 0.614 0.018 0.5 03/22/09 27,211,915.6 264.6 1,840.0 1,967.0 185 60.00 0.777 0.024 0.3 03/22/09 25,400,751.3 263.2 1,840.0 1,808.4 171 60.00 0.438 0.013 0.5 03/22/09 23,903,476.1 264.3 1,840.0 1,675.8 157 60.00 0.267 0.007 0.9 03/22/09 26,280,980.8 265.51,840.0 1,885.4 173 60.00 0.435 0.013 1.5 03/22/09 25,626,950.7 267.1 1,840.0 1,824.5 173 60.00 0.789 0.023 0.7 03/22/09 27,005,441.2 267.2 1,840.0 1,952.0 184 60.00 1.295 0.040 0.6 03/22/09 26,094,663.0 265.2 1,840.0 1,886.2 174 60.00 0.604 0.018 0.7 03/22/09 25,706,361.8 264.3 1,840.0 1,858.1 171 60.00 0.518 0.015 0.6 03/22/09 23,752,265.4 262.51,840.0 1,716.9 156 60.00 0.604 0.017 0.4 03/22/09 23,538,103.3 261.9 1,840.0 1,675.8 154 60.00 0.526 0.014 03/22/09 23,641,103.2 263.0 1,840.0 1,683.1 154 60.00 0.351 0.009

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 1.5 0.7 03/25/09 36,274,430.8 272.1 1,840.02,602.3 250 60.00 1.305 0.054 0.6 03/25/09 29,755,768.9 268.2 1,840.02,102.3 206 60.00 0.618 0.021 0.4 03/25/09 28,561,403.5 265.1 1,840.0 1,986.9 190 60.00 0.538 0.017 0.6 03/25/09 24,239,744.6 262.4 1,840.0 1,646.7 160 60.00 0.367 0.010 0.7 03/25/09 23,237,245.0 261.3 1,840.0 1,603.9 153 60.00 0.542 0.014 0.7 03/25/09 23,841,550.0 262.9 1,840.0 1,632.7 160 60.00 0.638 0.017 0.7 03/24/09 24,811,870.4 264.1 1,840.0 1,726.1 169 60.00 0.628 0.017 0.9 03/24/09 26,241,830.1 264.6 1,840.0 1,811.3 177 60.00 0.633 0.018 1.8 03/24/09 25,223,468.3 266.3 1,840.0 1,740.9 171 60.00 0.814 0.023 3.0 03/24/09 30,194,481.0 273.7 1,840.02,133.3 212 60.00 1.590 0.054 2.5 03/24/09 38,495,657.5 278.3 1,840.02,740.7 269 60.00 2.629 0.115 2.1 03/24/09 39,819,061.2 279.0 1,840.02,834.9 277 60.00 2.191 0.099 1.6 03/24/09 38,351,059.1 277.1 1,840.02,709.6 265 60.00 1.855 0.080 0.9 03/24/09 38,841,426.4 277.1 1,840.02,765.3 268 60.00 1.402 0.062 0.3 03/24/09 35,106,092.9 273.2 1,840.02,499.4 240 60.00 0.789 0.032 0.5 03/24/09 35,520,659.9 273.6 1,840.02,528.9 244 60.00 0.263 0.011 1.1 03/24/09 35,931,700.2 275.51,840.02,577.7 248 60.00 0.435 0.018 0.7 03/24/09 37,722,045.2 277.0 1,840.02,685.6 261 60.00 0.964 0.041 0.7 03/24/09 38,273,046.0 276.9 1,840.02,745.7 268 60.00 0.609 0.027 0.7 03/24/09 39,525,825.1 278.4 1,840.02,835.6 276 60.00 0.609 0.028 0.8 03/24/09 39,810,400.5 278.8 1,840.02,834.3 277 60.00 0.614 0.028 0.5 03/24/09 39,436,846.7 277.51,840.02,829.2 274 60.00 0.696 0.031 0.2 03/24/09 38,769,298.1 276.51,840.02,802.3 270 60.00 0.432 0.019 0.4 03/24/09 36,122,291.1 271.1 1,840.02,552.1 241 60.00 0.177 0.007 0.9 03/24/09 26,237,983.9 264.7 1,840.0 1,868.0 173 60.00 0.351 0.010 1.2 03/24/09 24,179,483.7 264.3 1,840.0 1,695.2 159 60.00 0.801 0.022 0.8 03/24/09 24,375,040.7 263.7 1,840.0 1,708.9 163 60.00 1.068 0.029 0.8 03/24/09 23,140,843.2 262.6 1,840.0 1,647.5 157 60.00 0.701 0.018 0.6 03/24/09 22,712,835.4 262.0 1,840.0 1,629.4 151 60.00 0.696 0.018 3.9 03/24/09 22,955,739.1 262.9 1,840.0 1,646.8 154 60.00 0.522 0.014 0.9 03/23/09 23,223,584.2 264.0 1,840.0 1,653.4 156 60.00 3.418 0.090 1.5 03/23/09 23,697,559.7 265.1 1,840.0 1,700.1 159 60.00 0.783 0.021 2.3 03/23/09 27,503,748.2 267.9 1,840.0 1,973.1 190 60.00 1.305 0.041 2.6 03/23/09 29,905,668.1 272.0 1,840.02,177.9 210 60.00 1.971 0.069 1.8 03/23/09 35,874,586.2 275.6 1,840.02,671.1 253 60.00 2.179 0.093 0.8 03/23/09 33,538,141.2 270.8 1,840.02,478.9 236 60.00 1.520 0.060 03/23/09 31,512,236.1 268.0 1,840.02,294.9 219 60.00 0.685 0.025

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 C 08:00 S S SC 09:00 C 10:00 11:00 S S S 12:00 C 13:00 S S SC 14:00 C 15:00 C 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 3.1 2.8 03/26/09 37,661,094.4 277.4 1,840.02,660.8 257 60.00 2.738 0.116 2.4 03/26/09 38,200,882.8 278.2 1,840.02,678.2 258 60.00 2.492 0.107 2.7 03/26/09 36,733,275.8 275.0 1,840.02,535.4 241 60.00 2.170 0.088 3.5 03/26/09 37,016,024.7 277.1 1,840.02,595.1 245 60.00 2.403 0.100 3.8 03/26/09 37,428,486.8 277.4 1,840.02,644.4 251 60.00 3.091 0.131 4.1 03/26/09 37,098,231.2 277.4 1,840.02,641.2 250 60.00 3.331 0.141 3.7 03/26/09 38,560,423.4 277.51,840.02,766.3 262 60.00 3.566 0.158 3.4 03/26/09 38,558,442.3 278.4 1,840.02,745.2 261 60.00 3.243 0.142 3.4 03/26/09 38,164,322.8 278.9 1,840.02,758.6 262 60.00 2.935 0.129 3.4 03/26/09 38,544,327.5 279.7 1,840.02,786.1 263 60.00 2.935 0.131 3.1 03/26/09 38,268,490.6 279.7 1,840.02,786.9 262 60.00 2.913 0.130 2.4 03/26/09 37,781,508.8 278.0 1,840.02,731.0 255 60.00 2.676 0.117 1.4 03/26/09 36,815,875.6 277.2 1,840.02,641.1 245 60.00 2.088 0.088 1.6 03/26/09 30,164,805.5 267.8 1,840.02,131.2 194 60.00 1.236 0.042 1.2 03/26/09 24,418,034.5 264.51,840.0 1,658.8 156 60.00 1.470 0.039 1.2 03/26/09 24,130,662.2 263.9 1,840.0 1,678.7 159 60.00 1.076 0.029 4.7 03/26/09 23,335,058.4 263.4 1,840.0 1,610.6 156 60.00 1.085 0.028 4.7 03/26/09 23,544,776.8 265.4 1,840.0 1,612.3 156 60.00 4.283 0.110 4.7 03/26/09 26,276,027.9 268.8 1,840.0 1,799.3 174 60.00 4.283 0.123 3.1 03/25/09 28,489,659.8 269.51,840.0 1,997.4 189 60.00 4.183 0.134 3.7 03/25/09 31,242,871.5 275.9 1,840.02,122.5 208 60.00 2.847 0.097 3.7 03/25/09 37,731,623.6 280.2 1,840.02,645.3 251 60.00 3.293 0.139 4.2 03/25/09 37,853,175.6 279.8 1,840.02,633.3 250 60.00 3.319 0.140 4.4 03/25/09 38,201,396.3 281.1 1,840.02,657.5 254 60.00 3.767 0.160 4.7 03/25/09 38,509,903.0 280.6 1,840.02,699.9 258 60.00 3.916 0.169 4.3 03/25/09 38,682,808.1 279.2 1,840.02,733.0 260 60.00 4.151 0.181 3.9 03/25/09 38,861,835.7 273.51,840.02,745.7 262 60.00 3.798 0.167 3.4 03/25/09 33,426,097.1 254.7 1,840.02,416.1 225 60.00 3.367 0.130 3.9 03/25/09 28,103,475.7 230.4 1,840.0 1,664.8 149 60.00 3.581 0.095 1.6 03/25/09 24,621,106.4 208.2 1,840.0 1,217.7 104 60.00 4.921 0.096 3.9 03/25/09 21,414,478.2 203.6 1,840.0 849.6 70 60.00 2.517 0.034 0.1 03/25/09 24,726,510.6 203.3 1,840.0 215.0 7 48.00 27.986 0.077 3.0 03/25/09 27,832,040.1 232.9 1,840.0 151.3 9 46.00 1.148 0.002 3.9 03/25/09 41,087,255.2 279.3 1,840.02,858.2 277 27.00 2.691 0.055 2.6 03/25/09 40,393,002.6 279.8 1,840.02,853.9 277 60.00 3.444 0.157 2.2 03/25/09 40,497,042.4 279.6 1,840.02,861.2 277 60.00 2.296 0.105 03/25/09 40,222,120.4 279.3 1,840.02,863.6 277 60.00 1.928 0.088

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 01:00 C 02:00 C S S SC 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 2.1 1.7 03/28/09 36,424,469.0 270.8 1,840.02,474.5 240 60.00 1.929 0.076 1.3 03/28/09 34,859,392.3 268.4 1,840.02,330.2 224 60.00 1.587 0.059 0.8 03/28/09 31,373,032.5 266.4 1,840.02,097.2 200 60.00 1.214 0.041 1.4 03/28/09 30,092,401.9 266.3 1,840.02,093.4 198 60.00 0.718 0.024 1.2 03/28/09 29,023,471.5 266.8 1,840.02,003.2 197 60.00 1.266 0.041 1.0 03/28/09 30,285,675.7 267.2 1,840.02,139.8 210 60.00 1.060 0.036 1.5 03/28/09 29,875,372.7 268.4 1,840.02,143.2 209 60.00 0.870 0.030 4.7 03/28/09 29,288,131.1 268.0 1,840.02,085.2 200 60.00 1.315 0.044 1.1 03/27/09 32,758,328.2 271.3 1,840.02,278.8 217 60.00 4.216 0.154 1.8 03/27/09 31,199,857.4 267.1 1,840.02,255.2 213 60.00 0.950 0.034 2.0 03/27/09 27,831,819.5 266.1 1,840.0 1,981.5 192 60.00 1.578 0.050 1.9 03/27/09 32,094,185.4 269.51,840.02,180.3 211 60.00 1.837 0.064 1.1 03/27/09 35,869,417.3 273.7 1,840.02,534.2 243 60.00 1.678 0.068 1.0 03/27/09 32,094,777.4 266.3 1,840.02,267.6 212 60.00 0.972 0.035 1.9 03/27/09 25,243,089.6 263.6 1,840.0 1,769.8 165 60.00 0.890 0.025 1.9 03/27/09 26,859,861.9 264.7 1,840.0 1,868.5 180 60.00 1.704 0.051 2.2 03/27/09 29,516,353.2 269.1 1,840.02,101.4 202 60.00 1.665 0.056 2.5 03/27/09 34,438,088.8 274.1 1,840.02,433.1 231 60.00 1.943 0.076 2.4 03/27/09 37,746,981.8 277.0 1,840.02,707.9 253 60.00 2.175 0.094 2.6 03/27/09 38,578,306.5 278.1 1,840.02,788.5 261 60.00 2.072 0.092 2.8 03/27/09 38,254,280.5 277.7 1,840.02,765.1 260 60.00 2.245 0.099 2.5 03/27/09 37,753,514.0 277.3 1,840.02,729.0 259 60.00 2.417 0.105 2.4 03/27/09 38,763,581.6 278.2 1,840.02,844.1 268 60.00 2.126 0.097 2.1 03/27/09 39,216,590.1 279.0 1,840.02,898.6 273 60.00 2.026 0.094 1.5 03/27/09 39,310,154.7 278.1 1,840.02,905.5 271 60.00 1.773 0.082 1.2 03/27/09 36,668,632.0 272.4 1,840.02,670.5 248 60.00 1.285 0.055 1.1 03/27/09 29,572,994.1 265.1 1,840.02,073.3 191 60.00 1.068 0.035 1.0 03/27/09 24,796,437.2 263.0 1,840.0 1,698.0 158 60.00 1.002 0.027 4.7 03/27/09 24,402,989.8 263.7 1,840.0 1,671.1 159 60.00 0.911 0.024 0.9 03/27/09 25,986,012.5 263.7 1,840.0 1,779.5 170 60.00 4.283 0.122 0.9 03/27/09 24,127,077.7 263.0 1,840.0 1,665.3 154 60.00 0.814 0.022 1.0 03/27/09 23,869,069.9 262.6 1,840.0 1,634.5 154 60.00 0.820 0.021 1.6 03/26/09 24,379,240.9 264.3 1,840.0 1,682.7 165 60.00 0.904 0.024 2.3 03/26/09 26,354,222.4 268.1 1,840.0 1,833.3 179 60.00 1.435 0.042 2.7 03/26/09 33,966,611.8 273.8 1,840.02,307.5 222 60.00 2.113 0.078 3.4 03/26/09 36,132,330.9 275.9 1,840.02,474.3 236 60.00 2.460 0.097 03/26/09 37,748,388.1 278.0 1,840.02,646.5 254 60.00 3.026 0.128

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 1.9 2.7 03/29/09 32,356,033.7 271.9 1,840.02,286.0 226 60.00 1.678 0.061 1.9 03/29/09 37,626,013.2 275.0 1,840.02,699.3 261 60.00 2.349 0.101 1.3 03/29/09 35,381,785.5 270.9 1,840.02,538.3 243 60.00 1.653 0.067 1.3 03/29/09 28,540,698.5 266.4 1,840.02,032.0 197 60.00 1.139 0.037 1.6 03/29/09 28,001,086.3 265.51,840.0 1,993.5 191 60.00 1.139 0.036 2.1 03/29/09 25,992,655.3 264.7 1,840.0 1,836.5 181 60.00 1.413 0.041 2.3 03/29/09 30,119,860.3 269.0 1,840.02,160.8 210 60.00 1.827 0.063 2.8 03/29/09 34,152,290.3 271.6 1,840.02,412.9 232 60.00 2.031 0.078 3.3 03/29/09 35,995,331.2 274.1 1,840.02,523.6 244 60.00 2.492 0.101 2.8 03/29/09 37,928,356.5 274.4 1,840.02,638.5 258 60.00 2.960 0.125 2.2 03/29/09 38,415,683.3 273.8 1,840.02,609.8 258 60.00 2.572 0.107 2.4 03/29/09 37,489,659.1 273.51,840.02,567.3 252 60.00 2.005 0.082 2.4 03/29/09 37,564,323.2 273.6 1,840.02,572.3 252 60.00 2.187 0.090 2.5 03/29/09 34,547,233.6 269.4 1,840.02,422.0 232 60.00 2.136 0.083 2.7 03/29/09 31,885,022.1 268.4 1,840.02,252.7 216 60.00 2.208 0.080 2.3 03/29/09 31,392,528.1 266.4 1,840.02,183.9 211 60.00 2.422 0.085 2.2 03/29/09 32,174,842.1 267.1 1,840.02,238.3 213 60.00 2.063 0.074 2.2 03/29/09 31,895,848.7 267.0 1,840.02,218.9 211 60.00 1.973 0.070 2.4 03/29/09 28,513,448.3 261.9 1,840.0 1,937.0 185 60.00 2.021 0.063 2.2 03/29/09 25,889,583.8 261.1 1,840.0 1,758.8 172 60.00 2.204 0.062 1.9 03/29/09 29,260,907.4 265.7 1,840.0 1,987.8 194 60.00 2.021 0.064 2.2 03/28/09 29,668,329.5 264.0 1,840.02,047.7 193 60.00 1.718 0.056 2.8 03/28/09 27,256,945.0 264.9 1,840.0 1,836.9 177 60.00 2.037 0.060 3.2 03/28/09 30,162,312.3 266.3 1,840.02,114.6 203 60.00 2.492 0.084 3.2 03/28/09 32,514,417.8 269.0 1,840.02,226.5 213 60.00 2.916 0.104 3.3 03/28/09 34,294,499.7 271.3 1,840.02,348.4 226 60.00 2.916 0.109 3.2 03/28/09 36,122,069.9 273.51,840.02,493.2 240 60.00 2.983 0.119 2.6 03/28/09 36,933,489.8 273.1 1,840.02,589.3 250 60.00 2.848 0.118 2.1 03/28/09 36,523,745.0 274.6 1,840.02,560.7 246 60.00 2.314 0.095 2.2 03/28/09 37,729,007.9 273.7 1,840.02,645.1 253 60.00 1.869 0.079 2.2 03/28/09 34,516,558.3 272.2 1,840.02,419.9 230 60.00 1.958 0.076 2.3 03/28/09 35,216,758.6 273.9 1,840.02,507.3 241 60.00 1.928 0.077 2.1 03/28/09 37,153,905.7 274.7 1,840.02,685.6 257 60.00 1.986 0.085 1.9 03/28/09 37,051,622.4 274.51,840.02,658.1 255 60.00 1.827 0.078 1.8 03/28/09 36,586,391.1 274.8 1,840.02,604.8 249 60.00 1.665 0.069 2.0 03/28/09 37,689,537.6 275.9 1,840.02,683.4 258 60.00 1.578 0.068 03/28/09 37,458,728.8 274.9 1,840.02,666.9 255 60.00 1.753 0.075

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 2.6 2.8 03/31/09 36,207,074.8 272.7 1,840.02,459.7 240 60.00 2.388 0.094 3.1 03/31/09 36,604,564.0 274.51,840.02,466.9 243 60.00 2.593 0.102 2.7 03/31/09 37,413,991.0 274.7 1,840.02,562.0 249 60.00 2.825 0.116 2.5 03/31/09 36,118,754.9 271.8 1,840.02,473.4 239 60.00 2.460 0.097 1.4 03/31/09 32,845,013.1 269.3 1,840.02,284.9 222 60.00 2.242 0.082 1.4 03/31/09 30,871,600.1 267.9 1,840.02,181.2 208 60.00 1.236 0.043 1.4 03/31/09 26,726,212.0 265.2 1,840.0 1,859.2 178 60.00 1.256 0.037 1.5 03/31/09 26,250,034.1 262.0 1,840.0 1,697.7 166 60.00 1.351 0.037 1.4 03/31/09 25,088,849.8 260.2 1,840.0 1,636.2 158 60.00 1.435 0.038 1.3 03/31/09 25,548,728.7 264.0 1,840.0 1,749.6 174 60.00 1.276 0.036 1.3 03/30/09 26,859,950.3 261.51,840.0 1,795.5 170 60.00 1.214 0.035 1.8 03/30/09 26,064,622.4 263.3 1,840.0 1,784.9 171 60.00 1.185 0.034 2.1 03/30/09 27,317,471.5 264.8 1,840.0 1,915.2 187 60.00 1.602 0.049 2.7 03/30/09 31,979,774.3 269.0 1,840.02,207.3 216 60.00 1.899 0.067 2.7 03/30/09 34,248,106.9 272.0 1,840.02,401.1 232 60.00 2.403 0.092 1.8 03/30/09 36,890,731.1 271.1 1,840.02,546.3 245 60.00 2.441 0.099 2.8 03/30/09 29,452,145.4 263.9 1,840.02,096.9 197 60.00 1.578 0.053 2.5 03/30/09 28,897,223.1 265.0 1,840.0 1,994.5 194 60.00 2.531 0.081 2.1 03/30/09 30,656,929.9 266.51,840.02,182.6 210 60.00 2.191 0.076 2.4 03/30/09 31,504,918.9 269.51,840.02,328.6 219 60.00 1.773 0.066 3.0 03/30/09 33,569,048.1 271.8 1,840.02,444.7 230 60.00 2.056 0.080 3.3 03/30/09 35,632,569.8 274.1 1,840.02,595.0 243 60.00 2.571 0.107 3.3 03/30/09 35,287,632.9 272.9 1,840.02,589.1 241 60.00 2.807 0.116 3.2 03/30/09 35,147,308.0 272.2 1,840.02,540.5 240 60.00 2.849 0.116 3.4 03/30/09 36,357,567.3 273.51,840.02,628.1 248 60.00 2.762 0.116 3.5 03/30/09 37,267,095.7 274.6 1,840.02,653.2 253 60.00 2.980 0.126 3.6 03/30/09 37,291,607.7 274.8 1,840.02,655.0 253 60.00 3.068 0.130 3.6 03/30/09 37,729,138.4 275.2 1,840.02,686.1 256 60.00 3.155 0.136 3.2 03/30/09 37,117,095.4 273.3 1,840.02,662.7 254 60.00 3.131 0.133 2.7 03/30/09 33,891,093.0 268.8 1,840.02,412.9 229 60.00 2.805 0.108 2.0 03/30/09 31,797,109.0 268.1 1,840.02,229.2 212 60.00 2.403 0.086 1.7 03/30/09 30,335,828.7 265.7 1,840.02,143.3 206 60.00 1.766 0.061 1.9 03/30/09 25,867,341.4 264.1 1,840.0 1,827.6 177 60.00 1.501 0.044 4.7 03/30/09 27,058,129.4 264.7 1,840.0 1,941.1 187 60.00 1.653 0.051 2.2 03/29/09 27,991,666.9 267.3 1,840.0 1,992.9 195 60.00 4.119 0.131 2.0 03/29/09 31,637,887.9 269.2 1,840.02,252.5 217 60.00 1.928 0.069 03/29/09 33,380,106.8 269.7 1,840.02,412.8 229 60.00 1.727 0.067

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 1.1 1.2 04/01/09 26,040,776.8 265.2 1,840.0 1,825.7 176 60.00 0.979 0.029 1.4 04/01/09 29,170,008.6 267.3 1,840.02,076.8 202 60.00 1.052 0.035 1.6 04/01/09 32,695,696.6 271.4 1,840.02,363.4 224 60.00 1.209 0.046 1.3 04/01/09 35,278,996.3 273.3 1,840.02,550.1 241 60.00 1.381 0.056 1.1 04/01/09 34,204,724.0 270.2 1,840.02,453.8 231 60.00 1.131 0.044 1.0 04/01/09 30,134,482.4 267.8 1,840.02,178.2 209 60.00 0.950 0.033 1.4 04/01/09 29,696,241.9 265.51,840.02,162.6 204 60.00 0.857 0.030 1.4 04/01/09 26,456,404.3 265.7 1,840.0 1,883.6 183 60.00 1.227 0.037 1.5 04/01/09 31,077,130.5 268.4 1,840.02,246.3 211 60.00 1.209 0.043 1.6 04/01/09 31,847,406.4 270.1 1,840.02,267.4 216 60.00 1.315 0.048 2.0 04/01/09 34,622,490.4 273.3 1,840.02,464.9 234 60.00 1.402 0.055 2.1 04/01/09 36,482,942.2 275.4 1,840.02,676.7 252 60.00 1.701 0.073 2.0 04/01/09 36,439,826.5 273.6 1,840.02,634.0 251 60.00 1.813 0.076 1.6 04/01/09 35,970,451.6 272.6 1,840.02,600.0 249 60.00 1.727 0.072 1.6 04/01/09 34,750,241.9 272.6 1,840.02,511.8 238 60.00 1.381 0.055 1.3 04/01/09 35,576,672.9 274.3 1,840.02,552.3 244 60.00 1.392 0.057 1.0 04/01/09 35,595,534.2 270.7 1,840.02,534.3 241 60.00 1.139 0.046 0.7 04/01/09 27,167,960.4 261.8 1,840.0 1,830.9 179 60.00 0.926 0.027 0.8 04/01/09 23,884,485.0 260.6 1,840.0 1,648.5 159 60.00 0.633 0.017 1.0 04/01/09 23,760,000.1 263.3 1,840.0 1,627.0 159 60.00 0.729 0.019 4.7 04/01/09 27,944,373.2 265.0 1,840.0 1,883.2 188 60.00 0.926 0.028 4.7 04/01/09 26,429,637.3 263.51,840.0 1,795.5 174 60.00 4.317 0.124 4.7 04/01/09 26,417,654.5 265.1 1,840.0 1,794.7 178 60.00 4.317 0.124 1.2 03/31/09 30,835,107.4 266.8 1,840.02,111.5 208 60.00 4.283 0.145 1.3 03/31/09 32,094,460.3 268.4 1,840.02,197.7 215 60.00 1.093 0.038 1.5 03/31/09 31,937,404.4 267.8 1,840.02,204.3 212 60.00 1.175 0.041 1.7 03/31/09 31,230,308.8 268.9 1,840.02,121.6 207 60.00 1.378 0.047 1.6 03/31/09 33,621,860.3 270.4 1,840.02,338.9 225 60.00 1.525 0.057 0.9 03/31/09 36,344,598.8 271.9 1,840.02,528.3 244 60.00 1.435 0.058 1.2 03/31/09 35,136,754.1 270.2 1,840.02,444.3 235 60.00 0.807 0.032 1.5 03/31/09 33,501,090.1 270.9 1,840.02,385.1 228 60.00 1.052 0.040 1.8 03/31/09 34,255,471.9 270.8 1,840.02,438.8 231 60.00 1.315 0.051 2.5 03/31/09 33,712,345.2 271.8 1,840.02,381.8 229 60.00 1.590 0.061 2.7 03/31/09 35,727,176.5 273.6 1,840.02,524.2 242 60.00 2.208 0.089 3.2 03/31/09 36,180,724.6 274.4 1,840.02,556.3 244 60.00 2.385 0.097 2.9 03/31/09 36,023,012.3 272.4 1,840.02,486.4 241 60.00 2.893 0.115 03/31/09 37,271,041.8 273.7 1,840.02,572.5 250 60.00 2.622 0.108

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 C 02:00 C S S SC 03:00 S S SC 04:00 S S SC 05:00 C C 06:00 07:00 ST ST STC 08:00 C 09:00 10:00 11:00 0.7 1.1 04/03/09 35,031,103.5 273.1 1,840.02,551.2 242 60.00 0.600 0.024 1.0 04/03/09 36,973,961.7 273.7 1,840.02,712.8 255 60.00 0.936 0.041 0.9 04/03/09 36,372,742.4 272.1 1,840.02,648.9 252 60.00 0.857 0.036 4.7 04/03/09 36,452,364.8 272.8 1,840.02,674.5 253 60.00 0.765 0.033 1.6 04/03/09 36,887,224.3 273.7 1,840.02,706.4 256 60.00 3.997 0.173 1.5 04/03/09 36,660,816.1 273.6 1,840.02,689.8 254 60.00 1.361 0.059 4.7 04/03/09 35,736,567.1 271.8 1,840.02,641.4 247 60.00 1.266 0.053 4.7 04/03/09 31,461,054.1 263.3 1,840.02,171.5 204 60.00 4.249 0.148 4.7 04/03/09 26,200,435.9 259.3 1,840.0 1,765.7 169 60.00 4.352 0.123 0.7 04/03/09 23,827,107.6 259.1 1,840.0 1,592.8 151 60.00 4.387 0.112 4.7 04/03/09 23,968,592.6 259.6 1,840.0 1,589.2 151 60.00 0.659 0.017 4.7 04/03/09 24,618,040.7 259.8 1,840.0 1,605.5 153 60.00 4.497 0.115 1.2 04/02/09 24,816,176.5 260.4 1,840.0 1,631.9 159 60.00 4.460 0.116 1.4 04/02/09 25,705,439.5 261.0 1,840.0 1,718.3 166 60.00 1.120 0.031 1.7 04/02/09 29,642,143.7 267.7 1,840.0 1,997.6 197 60.00 1.296 0.041 1.9 04/02/09 34,637,971.4 271.1 1,840.02,371.9 229 60.00 1.549 0.059 2.2 04/02/09 36,879,185.1 273.6 1,840.02,585.5 247 60.00 1.691 0.070 2.1 04/02/09 37,201,312.5 273.9 1,840.02,628.3 252 60.00 1.943 0.082 1.8 04/02/09 35,804,934.3 270.8 1,840.02,510.2 240 60.00 1.869 0.075 1.8 04/02/09 34,102,340.7 270.2 1,840.02,372.3 227 60.00 1.615 0.061 1.9 04/02/09 35,114,280.1 272.1 1,840.02,461.8 235 60.00 1.602 0.063 1.8 04/02/09 35,802,584.8 271.2 1,840.02,529.6 239 60.00 1.678 0.068 1.6 04/02/09 32,221,374.3 268.0 1,840.02,241.5 213 60.00 1.615 0.058 1.9 04/02/09 33,319,483.5 271.2 1,840.02,336.0 223 60.00 1.424 0.053 2.1 04/02/09 36,206,404.2 273.6 1,840.02,558.0 243 60.00 1.678 0.069 1.8 04/02/09 36,543,982.2 272.6 1,840.02,601.8 248 60.00 1.841 0.077 1.9 04/02/09 35,401,946.9 271.3 1,840.02,501.2 237 60.00 1.590 0.064 1.7 04/02/09 36,649,789.7 274.0 1,840.02,589.4 247 60.00 1.678 0.069 1.7 04/02/09 36,831,016.2 273.3 1,840.02,622.2 248 60.00 1.490 0.062 1.3 04/02/09 36,527,698.3 271.6 1,840.02,600.6 246 60.00 1.490 0.062 0.9 04/02/09 35,734,544.6 271.1 1,840.02,485.9 238 60.00 1.166 0.046 0.8 04/02/09 31,196,610.8 267.1 1,840.02,221.1 208 60.00 0.789 0.028 0.8 04/02/09 26,560,831.2 262.8 1,840.0 1,847.7 174 60.00 0.718 0.021 0.9 04/02/09 23,253,645.3 260.2 1,840.0 1,605.0 154 60.00 0.723 0.019 0.6 04/02/09 23,301,225.3 259.7 1,840.0 1,620.9 153 60.00 0.807 0.021 0.7 04/02/09 23,210,467.8 261.51,840.0 1,602.0 155 60.00 0.542 0.014 04/01/09 24,886,239.4 263.1 1,840.0 1,731.2 166 60.00 0.628 0.017

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 0.8 4.7 04/05/09 23,543,145.0 260.7 1,840.0 1,650.6 155 60.00 0.712 0.019 1.4 04/04/09 23,570,491.4 261.0 1,840.0 1,652.5 154 60.00 4.183 0.111 1.4 04/04/09 24,846,830.3 263.51,840.0 1,742.0 170 60.00 1.246 0.035 2.1 04/04/09 28,833,680.2 268.2 1,840.02,068.5 202 60.00 1.218 0.040 1.2 04/04/09 32,785,195.6 270.51,840.02,441.1 231 60.00 1.760 0.069 0.9 04/04/09 33,323,498.0 273.2 1,840.02,463.0 233 60.00 1.013 0.040 0.7 04/04/09 36,109,293.2 272.4 1,840.02,688.6 248 60.00 0.754 0.032 1.1 04/04/09 31,320,317.5 268.1 1,840.02,280.9 212 60.00 0.600 0.022 0.5 04/04/09 30,461,129.2 267.3 1,840.02,234.9 213 60.00 0.936 0.033 0.4 04/04/09 31,516,143.8 270.0 1,840.02,295.2 219 60.00 0.428 0.016 0.5 04/04/09 30,282,550.2 267.8 1,840.02,221.9 209 60.00 0.340 0.012 0.5 04/04/09 28,889,658.1 266.8 1,840.02,119.6 201 60.00 0.425 0.014 1.4 04/04/09 29,222,345.7 265.9 1,840.02,112.2 207 60.00 0.432 0.015 1.5 04/04/09 28,491,589.4 264.7 1,840.0 1,982.1 194 60.00 1.256 0.040 1.1 04/04/09 30,954,587.3 267.51,840.02,220.7 214 60.00 1.305 0.046 0.9 04/04/09 31,811,833.1 269.3 1,840.02,316.7 216 60.00 0.943 0.035 0.8 04/04/09 33,596,834.1 270.8 1,840.02,446.7 227 60.00 0.771 0.030 0.8 04/04/09 33,718,211.1 272.3 1,840.02,473.9 230 60.00 0.680 0.027 0.8 04/04/09 32,666,187.5 268.1 1,840.02,467.7 225 60.00 0.661 0.026 0.4 04/04/09 29,745,076.4 268.4 1,840.02,182.4 208 60.00 0.680 0.024 0.6 04/04/09 31,900,005.2 269.3 1,840.02,357.8 223 60.00 0.338 0.013 0.7 04/04/09 28,663,184.8 266.3 1,840.02,040.7 198 60.00 0.526 0.017 1.0 04/04/09 29,153,746.4 266.51,840.02,012.3 201 60.00 0.633 0.020 1.2 04/04/09 29,221,420.1 264.51,840.02,048.6 198 60.00 0.890 0.029 0.6 04/04/09 28,633,717.4 266.1 1,840.0 1,991.9 196 60.00 1.076 0.034 0.7 04/03/09 30,315,289.2 268.0 1,840.02,158.3 210 60.00 0.526 0.018 1.2 04/03/09 29,381,290.1 266.8 1,840.02,139.7 205 60.00 0.600 0.021 1.8 04/03/09 29,302,945.0 269.0 1,840.02,134.0 204 60.00 1.028 0.035 1.9 04/03/09 34,258,068.4 271.9 1,840.02,476.3 236 60.00 1.554 0.062 1.6 04/03/09 34,848,418.5 273.0 1,840.02,556.8 242 60.00 1.616 0.066 0.7 04/03/09 35,676,180.0 271.9 1,840.02,617.5 247 60.00 1.361 0.057 0.8 04/03/09 34,592,637.9 271.1 1,840.02,538.1 237 60.00 0.595 0.024 0.8 04/03/09 34,572,275.3 272.8 1,840.02,536.5 238 60.00 0.680 0.028 0.9 04/03/09 34,973,247.1 271.6 1,840.02,546.9 238 60.00 0.685 0.028 0.8 04/03/09 33,140,945.2 270.51,840.02,413.5 229 60.00 0.771 0.030 0.4 04/03/09 34,231,673.6 270.3 1,840.02,493.0 235 60.00 0.685 0.027 04/03/09 32,186,505.0 269.1 1,840.02,309.1 219 60.00 0.348 0.013

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 2.7 3.0 04/06/09 35,320,589.8 272.0 1,840.02,610.7 245 60.00 2.279 0.095 3.2 04/06/09 35,298,297.3 271.4 1,840.02,589.8 245 60.00 2.551 0.106 2.6 04/06/09 35,280,396.9 270.2 1,840.02,569.3 245 60.00 2.742 0.113 1.3 04/06/09 35,536,399.5 270.9 1,840.02,568.6 245 60.00 2.245 0.092 1.0 04/06/09 33,296,719.1 264.7 1,840.02,406.8 226 60.00 1.122 0.043 1.4 04/06/09 24,266,761.6 260.6 1,840.0 1,688.1 163 60.00 0.897 0.024 1.6 04/06/09 29,722,626.9 266.9 1,840.02,100.0 210 60.00 1.236 0.042 0.7 04/06/09 35,369,875.2 269.1 1,840.02,556.6 243 60.00 1.381 0.056 1.1 04/06/09 29,146,308.0 261.51,840.02,106.7 199 60.00 0.604 0.020 1.2 04/06/09 24,217,309.9 261.3 1,840.0 1,697.8 166 60.00 0.979 0.027 0.8 04/06/09 26,700,990.4 259.7 1,840.0 1,915.5 186 60.00 1.044 0.032 0.8 04/06/09 23,232,194.3 258.2 1,840.0 1,616.1 160 60.00 0.718 0.019 0.9 04/06/09 23,896,984.2 258.51,840.0 1,662.4 160 60.00 0.718 0.019 1.2 04/06/09 24,002,554.0 258.6 1,840.0 1,643.7 158 60.00 0.820 0.022 1.2 04/05/09 23,723,398.1 257.8 1,840.0 1,650.3 159 60.00 1.076 0.028 0.8 04/05/09 23,484,599.8 257.2 1,840.0 1,646.5 158 60.00 1.068 0.028 1.6 04/05/09 23,647,698.9 260.51,840.0 1,657.9 163 60.00 0.712 0.019 1.9 04/05/09 27,055,207.0 265.0 1,840.0 1,970.3 189 60.00 1.371 0.043 2.3 04/05/09 33,055,460.0 270.4 1,840.02,389.3 227 60.00 1.640 0.063 2.4 04/05/09 34,840,125.9 269.51,840.02,499.4 239 60.00 2.001 0.080 2.1 04/05/09 33,259,696.0 266.2 1,840.02,331.8 224 60.00 2.136 0.080 2.0 04/05/09 34,042,229.1 268.7 1,840.02,386.6 227 60.00 1.869 0.071 2.0 04/05/09 35,191,943.2 269.4 1,840.02,467.3 235 60.00 1.780 0.070 2.0 04/05/09 33,737,005.1 268.0 1,840.02,383.6 227 60.00 1.766 0.067 1.6 04/05/09 33,510,382.5 267.51,840.02,385.8 230 60.00 1.753 0.067 1.8 04/05/09 33,086,820.4 268.51,840.02,373.6 225 60.00 1.392 0.053 1.8 04/05/09 33,999,821.1 271.0 1,840.02,494.6 238 60.00 1.531 0.061 1.5 04/05/09 33,674,018.9 268.9 1,840.02,488.9 236 60.00 1.520 0.060 1.2 04/05/09 30,361,320.0 265.8 1,840.02,244.1 216 60.00 1.266 0.045 0.8 04/05/09 31,760,438.3 268.51,840.02,313.0 220 60.00 1.028 0.038 0.8 04/05/09 31,062,941.9 264.7 1,840.02,262.2 212 60.00 0.685 0.025 0.9 04/05/09 24,736,839.6 259.51,840.0 1,747.7 164 60.00 0.707 0.020 0.3 04/05/09 23,159,864.6 258.3 1,840.0 1,623.7 154 60.00 0.801 0.021 0.5 04/05/09 23,386,244.5 259.1 1,840.0 1,639.6 158 60.00 0.267 0.007 0.3 04/05/09 23,235,585.2 260.1 1,840.0 1,629.0 154 60.00 0.445 0.012 0.5 04/05/09 23,157,700.2 260.7 1,840.0 1,585.8 154 60.00 0.273 0.007 04/05/09 23,802,698.2 260.4 1,840.0 1,668.8 156 60.00 0.445 0.012

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 1.2 1.2 04/08/09 30,324,306.7 266.8 1,840.02,142.5 206 60.00 1.060 0.036 1.4 04/08/09 30,235,900.6 269.3 1,840.02,136.2 206 60.00 1.060 0.036 1.1 04/08/09 32,209,972.7 268.51,840.02,310.7 217 60.00 1.218 0.045 1.2 04/07/09 29,386,449.9 267.1 1,840.02,092.2 202 60.00 0.964 0.032 1.4 04/07/09 28,508,537.0 265.9 1,840.02,029.7 197 60.00 1.052 0.034 1.7 04/07/09 30,237,824.7 268.2 1,840.02,136.4 210 60.00 1.236 0.042 1.3 04/07/09 35,287,236.5 272.51,840.02,531.5 241 60.00 1.479 0.060 0.8 04/07/09 36,795,754.9 273.9 1,840.02,639.7 250 60.00 1.131 0.048 1.0 04/07/09 34,290,027.6 271.4 1,840.02,497.2 233 60.00 0.685 0.027 1.1 04/07/09 32,855,433.1 271.9 1,840.02,392.7 226 60.00 0.857 0.033 1.6 04/07/09 32,267,518.3 267.4 1,840.02,279.8 219 60.00 0.972 0.035 1.6 04/07/09 29,096,920.5 265.8 1,840.02,024.1 198 60.00 1.435 0.046 1.3 04/07/09 33,214,929.4 270.3 1,840.02,292.6 221 60.00 1.447 0.053 1.3 04/07/09 36,006,075.4 272.1 1,840.02,485.2 238 60.00 1.175 0.047 1.7 04/07/09 36,337,359.2 273.1 1,840.02,547.5 244 60.00 1.157 0.047 1.4 04/07/09 36,855,783.8 273.4 1,840.02,604.0 251 60.00 1.501 0.063 1.4 04/07/09 36,670,351.8 273.4 1,840.02,670.5 255 60.00 1.200 0.051 1.1 04/07/09 36,616,532.4 272.4 1,840.02,666.7 255 60.00 1.200 0.051 1.3 04/07/09 36,167,421.1 271.9 1,840.02,574.9 245 60.00 0.964 0.040 1.2 04/07/09 36,171,982.5 272.7 1,840.02,555.6 244 60.00 1.148 0.047 1.2 04/07/09 36,446,536.4 272.7 1,840.02,575.1 245 60.00 1.060 0.044 0.8 04/07/09 35,023,268.6 268.9 1,840.02,455.4 235 60.00 1.068 0.042 0.9 04/07/09 29,431,105.1 263.2 1,840.02,095.4 202 60.00 0.701 0.023 0.3 04/07/09 28,059,585.9 265.2 1,840.0 1,952.0 195 60.00 0.807 0.025 4.7 04/07/09 31,206,521.9 266.8 1,840.02,255.7 217 60.00 0.259 0.009 4.7 04/07/09 27,203,017.8 263.8 1,840.0 1,981.1 190 60.00 4.027 0.128 4.7 04/07/09 29,050,920.4 266.1 1,840.02,068.3 200 60.00 4.119 0.136 1.6 04/06/09 30,914,342.1 268.2 1,840.02,234.5 220 60.00 4.057 0.145 1.4 04/06/09 34,520,226.3 271.4 1,840.02,495.2 239 60.00 1.381 0.055 1.3 04/06/09 35,281,557.1 272.2 1,840.02,550.3 242 60.00 1.209 0.049 1.7 04/06/09 35,396,900.1 272.4 1,840.02,577.8 245 60.00 1.114 0.046 2.1 04/06/09 35,101,366.4 272.0 1,840.02,575.3 246 60.00 1.446 0.060 1.9 04/06/09 35,012,386.6 271.51,840.02,587.8 245 60.00 1.773 0.073 2.0 04/06/09 34,590,229.8 270.3 1,840.02,556.7 241 60.00 1.604 0.066 2.1 04/06/09 34,563,584.5 271.2 1,840.02,517.2 237 60.00 1.714 0.069 2.4 04/06/09 34,440,908.9 272.1 1,840.02,508.2 237 60.00 1.799 0.072 04/06/09 35,558,352.2 272.8 1,840.02,589.6 244 60.00 2.056 0.085

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 S S S 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 0.5 0.9 04/09/09 28,122,331.5 269.2 1,840.02,048.0 198 60.00 0.428 0.014 1.2 04/09/09 31,584,238.6 272.0 1,840.02,265.8 220 60.00 0.783 0.028 1.5 04/09/09 32,230,112.2 272.0 1,840.02,294.6 225 60.00 1.052 0.039 1.7 04/09/09 33,850,657.5 274.6 1,840.02,465.2 233 60.00 1.285 0.051 1.7 04/09/09 35,708,972.4 276.7 1,840.02,581.1 243 60.00 1.468 0.061 1.8 04/09/09 35,841,635.5 276.51,840.02,590.8 241 60.00 1.468 0.061 1.4 04/09/09 35,590,889.6 276.4 1,840.02,572.6 241 60.00 1.554 0.064 1.3 04/09/09 35,422,435.8 276.51,840.02,579.6 244 60.00 1.200 0.049 1.1 04/09/09 36,052,079.9 276.0 1,840.02,586.3 249 60.00 1.131 0.047 1.0 04/09/09 36,057,141.2 275.1 1,840.02,625.9 248 60.00 0.943 0.040 0.4 04/09/09 33,296,450.3 270.4 1,840.02,424.8 231 60.00 0.857 0.033 0.2 04/09/09 31,728,475.6 268.0 1,840.02,258.9 216 60.00 0.351 0.013 0.2 04/09/09 29,043,026.3 266.8 1,840.02,067.7 198 60.00 0.175 0.006 0.3 04/09/09 28,021,869.0 263.6 1,840.0 1,964.6 184 60.00 0.178 0.006 0.7 04/09/09 24,878,753.2 261.7 1,840.0 1,717.2 169 60.00 0.271 0.007 4.7 04/09/09 25,570,074.5 264.8 1,840.0 1,751.0 178 60.00 0.638 0.018 0.7 04/08/09 29,546,629.8 266.2 1,840.02,039.4 200 60.00 4.249 0.139 1.2 04/08/09 30,153,187.6 268.1 1,840.02,097.6 204 60.00 0.628 0.021 1.3 04/08/09 31,315,158.2 269.8 1,840.02,212.5 215 60.00 1.060 0.037 1.1 04/08/09 32,808,106.0 271.51,840.02,353.6 226 60.00 1.131 0.043 0.7 04/08/09 35,198,175.5 273.51,840.02,601.6 245 60.00 0.929 0.039 0.9 04/08/09 33,005,506.5 269.0 1,840.02,421.6 226 60.00 0.595 0.023 1.0 04/08/09 28,772,194.7 265.8 1,840.02,064.1 197 60.00 0.783 0.026 1.3 04/08/09 26,505,973.6 265.51,840.0 1,887.1 181 60.00 0.876 0.026 0.9 04/08/09 28,963,150.9 265.7 1,840.02,093.5 202 60.00 1.122 0.038 0.8 04/08/09 29,507,782.9 266.6 1,840.02,100.8 203 60.00 0.789 0.026 1.0 04/08/09 32,217,430.7 270.7 1,840.02,258.7 218 60.00 0.712 0.026 1.2 04/08/09 35,110,888.2 271.9 1,840.02,499.8 234 60.00 0.876 0.035 1.1 04/08/09 34,387,155.9 270.4 1,840.02,448.2 233 60.00 1.052 0.041 1.4 04/08/09 33,806,267.5 271.51,840.02,388.5 228 60.00 0.972 0.037 1.6 04/08/09 36,232,087.2 274.1 1,840.02,579.6 245 60.00 1.227 0.051 1.7 04/08/09 35,800,968.2 273.51,840.02,548.9 242 60.00 1.402 0.057 1.4 04/08/09 35,834,896.5 272.2 1,840.02,512.3 243 60.00 1.513 0.061 1.5 04/08/09 36,243,801.6 273.0 1,840.02,560.7 245 60.00 1.236 0.051 0.9 04/08/09 35,770,259.8 273.0 1,840.02,527.2 242 60.00 1.325 0.054 1.1 04/08/09 33,080,146.7 268.3 1,840.02,319.2 221 60.00 0.801 0.030 04/08/09 28,643,023.0 265.9 1,840.02,023.7 196 60.00 0.972 0.031

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 C 02:00 C S S SC 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C S S S 03:00 S S S 04:00 C 2.2 4.7 04/11/09 24,650,594.6 262.2 1,840.0 1,634.5 152 60.00 2.070 0.054 4.7 04/11/09 24,766,056.4 262.0 1,840.0 1,669.0 156 60.00 4.352 0.116 1.5 04/11/09 24,473,769.2 262.7 1,840.0 1,649.3 154 60.00 4.352 0.115 1.5 04/11/09 24,992,416.1 262.8 1,840.0 1,657.1 154 60.00 1.412 0.037 2.0 04/11/09 25,458,276.7 263.6 1,840.0 1,688.0 157 60.00 1.412 0.038 2.6 04/10/09 24,651,531.9 265.8 1,840.0 1,688.1 160 60.00 1.822 0.049 2.3 04/10/09 27,710,088.8 264.51,840.0 1,957.8 179 60.00 2.296 0.072 1.9 04/10/09 25,092,652.7 266.3 1,840.0 1,718.3 165 60.00 2.096 0.058 2.1 04/10/09 31,990,243.3 273.0 1,840.02,155.8 208 60.00 1.759 0.061 1.7 04/10/09 35,600,787.6 273.2 1,840.02,457.2 230 60.00 1.899 0.075 1.9 04/10/09 29,731,676.8 264.8 1,840.02,003.7 185 60.00 1.574 0.050 1.9 04/10/09 25,518,838.7 263.51,840.0 1,761.4 165 60.00 1.718 0.048 2.0 04/10/09 25,417,814.6 264.7 1,840.0 1,795.8 172 60.00 1.678 0.048 1.2 04/10/09 26,324,447.8 263.51,840.0 1,831.2 167 60.00 1.794 0.053 1.8 04/10/09 24,829,032.8 264.2 1,840.0 1,727.2 159 60.00 1.076 0.030 2.0 04/10/09 25,420,127.6 266.2 1,840.0 1,782.2 168 60.00 1.602 0.046 1.9 04/10/09 31,619,578.7 272.1 1,840.02,182.5 208 60.00 1.808 0.063 1.8 04/10/09 33,434,377.6 272.6 1,840.02,344.0 218 60.00 1.691 0.063 2.8 04/10/09 33,877,710.8 274.8 1,840.02,393.6 224 60.00 1.590 0.061 2.4 04/10/09 35,561,286.9 276.51,840.02,531.8 236 60.00 2.454 0.099 1.7 04/10/09 36,518,189.5 275.3 1,840.02,560.2 240 60.00 2.136 0.087 1.1 04/10/09 36,853,464.9 275.7 1,840.02,623.8 246 60.00 1.490 0.063 0.6 04/10/09 36,026,512.0 271.51,840.02,584.5 243 60.00 0.957 0.040 0.4 04/10/09 30,038,683.4 268.6 1,840.02,138.6 207 60.00 0.526 0.018 0.2 04/10/09 29,636,536.8 266.7 1,840.02,077.8 198 60.00 0.356 0.012 4.7 04/10/09 26,613,165.1 263.51,840.0 1,880.3 175 60.00 0.177 0.005 0.2 04/10/09 23,439,974.0 261.1 1,840.0 1,656.1 155 60.00 4.151 0.110 0.3 04/10/09 23,131,909.6 261.8 1,840.0 1,646.9 153 60.00 0.175 0.005 0.3 04/10/09 23,252,475.2 263.2 1,840.0 1,642.8 153 60.00 0.265 0.007 0.5 04/09/09 24,190,599.6 264.3 1,840.0 1,696.0 158 60.00 0.267 0.007 0.8 04/09/09 23,587,669.8 263.7 1,840.0 1,679.4 155 60.00 0.438 0.012 1.1 04/09/09 23,041,348.2 264.8 1,840.0 1,640.4 153 60.00 0.701 0.018 1.1 04/09/09 27,942,675.4 271.9 1,840.02,019.8 192 60.00 0.950 0.031 0.9 04/09/09 33,618,302.2 275.9 1,840.02,411.7 227 60.00 0.957 0.037 0.6 04/09/09 34,488,377.6 275.4 1,840.02,492.9 233 60.00 0.777 0.031 0.4 04/09/09 30,834,471.3 270.7 1,840.02,245.5 214 60.00 0.514 0.018 04/09/09 26,897,742.5 268.0 1,840.0 1,944.3 187 60.00 0.345 0.011

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 2.5 2.4 04/12/09 26,613,435.3 266.1 1,840.0 1,851.3 179 60.00 2.242 0.066 2.1 04/12/09 24,881,256.1 264.6 1,840.0 1,730.9 165 60.00 2.153 0.060 2.0 04/12/09 24,239,561.3 263.8 1,840.0 1,699.4 160 60.00 1.869 0.051 1.9 04/12/09 23,829,563.7 262.9 1,840.0 1,696.6 157 60.00 1.753 0.048 1.6 04/12/09 23,425,648.7 262.51,840.0 1,655.1 155 60.00 1.678 0.044 1.5 04/12/09 23,312,586.4 264.4 1,840.0 1,647.1 153 60.00 1.413 0.037 1.4 04/12/09 23,575,361.8 265.51,840.0 1,665.6 153 60.00 1.325 0.035 1.2 04/12/09 24,148,751.9 265.51,840.0 1,732.4 155 60.00 1.218 0.034 1.5 04/12/09 23,608,656.8 264.6 1,840.0 1,680.9 156 60.00 1.052 0.028 1.6 04/12/09 25,381,554.2 268.7 1,840.0 1,820.9 175 60.00 1.305 0.038 1.5 04/12/09 30,198,643.0 267.9 1,840.02,182.9 204 60.00 1.381 0.048 1.0 04/12/09 25,708,943.1 264.6 1,840.0 1,816.4 171 60.00 1.325 0.038 1.8 04/12/09 23,824,363.5 262.8 1,840.0 1,709.1 157 60.00 0.870 0.024 1.3 04/12/09 24,187,100.7 262.9 1,840.0 1,656.3 158 60.00 1.640 0.043 1.6 04/12/09 24,468,016.2 264.51,840.0 1,662.2 157 60.00 1.194 0.032 1.9 04/12/09 24,832,585.5 264.8 1,840.0 1,673.5 156 60.00 1.481 0.040 2.0 04/12/09 24,641,918.9 264.4 1,840.0 1,714.2 157 60.00 1.704 0.047 1.0 04/12/09 23,442,941.2 262.7 1,840.0 1,669.0 153 60.00 1.753 0.047 0.8 04/11/09 23,561,414.6 262.8 1,840.0 1,651.8 155 60.00 0.890 0.024 1.2 04/11/09 23,243,350.0 263.9 1,840.0 1,642.2 154 60.00 0.707 0.019 1.5 04/11/09 24,239,520.3 264.9 1,840.0 1,673.1 158 60.00 1.085 0.029 1.2 04/11/09 27,599,947.2 269.3 1,840.0 1,875.0 183 60.00 1.378 0.041 0.7 04/11/09 31,999,971.0 272.4 1,840.02,278.3 216 60.00 1.052 0.038 1.5 04/11/09 26,486,286.9 267.2 1,840.0 1,900.1 177 60.00 0.609 0.018 1.7 04/11/09 26,015,903.3 266.4 1,840.0 1,866.4 171 60.00 1.305 0.039 1.7 04/11/09 23,917,633.3 263.4 1,840.0 1,650.9 155 60.00 1.537 0.041 1.7 04/11/09 24,006,986.5 262.9 1,840.0 1,657.0 155 60.00 1.537 0.041 1.7 04/11/09 24,191,050.5 262.9 1,840.0 1,669.7 156 60.00 1.537 0.041 1.2 04/11/09 24,599,677.5 262.8 1,840.0 1,711.3 160 60.00 1.525 0.042 1.0 04/11/09 24,293,886.9 264.9 1,840.0 1,690.0 156 60.00 1.076 0.029 1.4 04/11/09 24,984,541.9 265.2 1,840.0 1,792.4 161 60.00 0.870 0.025 1.7 04/11/09 26,916,414.8 269.3 1,840.0 1,901.7 177 60.00 1.236 0.038 1.7 04/11/09 28,693,851.3 268.51,840.02,074.1 192 60.00 1.468 0.049 1.4 04/11/09 28,836,332.6 270.51,840.02,100.0 198 60.00 1.457 0.049 1.1 04/11/09 31,318,724.7 269.4 1,840.02,263.8 211 60.00 1.209 0.044 1.4 04/11/09 26,726,217.0 265.1 1,840.0 1,888.3 173 60.00 0.972 0.029 04/11/09 25,090,240.3 263.7 1,840.0 1,704.5 156 60.00 1.286 0.035

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 S S S 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 2.1 1.9 04/14/09 36,100,514.6 272.3 1,840.02,589.9 241 60.00 1.827 0.076 1.0 04/14/09 35,070,291.8 272.2 1,840.02,496.8 233 60.00 1.665 0.066 0.8 04/14/09 33,990,868.1 270.1 1,840.02,420.0 224 60.00 0.876 0.034 0.8 04/14/09 28,368,949.9 263.6 1,840.02,019.7 187 60.00 0.701 0.023 0.9 04/14/09 23,732,779.7 260.6 1,840.0 1,663.9 159 60.00 0.712 0.019 0.9 04/14/09 23,421,370.5 261.4 1,840.0 1,667.5 158 60.00 0.789 0.021 1.2 04/14/09 24,105,329.2 263.1 1,840.0 1,703.1 161 60.00 0.795 0.022 1.4 04/13/09 26,234,529.3 266.2 1,840.0 1,853.6 178 60.00 1.060 0.031 2.0 04/13/09 29,879,685.6 269.1 1,840.02,159.8 205 60.00 1.209 0.042 2.1 04/13/09 32,445,802.5 271.1 1,840.02,345.3 221 60.00 1.727 0.065 1.7 04/13/09 35,758,045.9 274.3 1,840.02,604.1 242 60.00 1.799 0.075 1.7 04/13/09 36,554,169.2 274.4 1,840.02,701.8 249 60.00 1.435 0.062 1.4 04/13/09 36,050,341.0 274.2 1,840.02,664.6 247 60.00 1.435 0.061 1.6 04/13/09 34,754,837.0 272.2 1,840.02,568.8 240 60.00 1.182 0.049 1.7 04/13/09 35,085,295.6 274.1 1,840.02,574.2 240 60.00 1.361 0.056 1.7 04/13/09 36,703,400.4 274.8 1,840.02,692.9 251 60.00 1.446 0.062 1.4 04/13/09 36,086,055.6 274.3 1,840.02,667.2 248 60.00 1.435 0.061 1.6 04/13/09 36,335,255.9 274.8 1,840.02,685.6 253 60.00 1.182 0.051 1.8 04/13/09 35,815,051.9 275.0 1,840.02,627.7 247 60.00 1.361 0.057 1.9 04/13/09 36,547,922.5 275.8 1,840.02,661.6 252 60.00 1.542 0.066 2.1 04/13/09 36,473,511.1 275.2 1,840.02,695.9 256 60.00 1.604 0.069 2.0 04/13/09 36,477,682.4 275.3 1,840.02,696.2 255 60.00 1.773 0.076 1.9 04/13/09 36,441,375.3 276.0 1,840.02,693.5 255 60.00 1.688 0.073 1.5 04/13/09 36,654,419.5 277.0 1,840.02,729.1 256 60.00 1.592 0.069 1.8 04/13/09 36,477,140.1 276.8 1,840.02,716.0 252 60.00 1.257 0.055 1.2 04/13/09 35,099,873.9 271.9 1,840.02,594.3 242 60.00 1.520 0.063 4.7 04/13/09 26,236,319.7 263.51,840.0 1,882.1 176 60.00 1.044 0.031 4.7 04/13/09 25,313,762.2 262.8 1,840.0 1,802.2 170 60.00 4.119 0.119 4.7 04/13/09 23,296,096.4 263.2 1,840.0 1,607.9 154 60.00 4.249 0.109 4.7 04/13/09 24,116,185.0 263.7 1,840.0 1,690.7 157 60.00 4.183 0.113 1.1 04/13/09 24,029,536.0 264.0 1,840.0 1,671.7 154 60.00 4.216 0.113 1.5 04/12/09 24,045,486.1 264.0 1,840.0 1,685.8 157 60.00 0.979 0.026 1.9 04/12/09 25,217,353.6 265.4 1,840.0 1,795.3 169 60.00 1.315 0.038 2.1 04/12/09 27,900,835.2 268.9 1,840.02,001.6 191 60.00 1.653 0.053 2.1 04/12/09 31,617,179.0 273.4 1,840.02,268.2 217 60.00 1.827 0.066 2.1 04/12/09 33,904,151.3 274.3 1,840.02,413.8 228 60.00 1.841 0.071 04/12/09 31,517,780.0 269.7 1,840.02,209.7 209 60.00 1.869 0.066

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C S S S 03:00 S S S 04:00 C 05:00 C C 06:00 07:00 08:00 M M 09:00 10:00 11:00 12:00 13:00 M M 14:00 15:00 16:00 17:00 18:00 19:00 1.9 1.2 04/15/09 33,761,578.1 273.3 1,840.02,440.4 233 60.00 1.640 0.064 1.0 04/15/09 34,135,626.9 268.7 1,840.02,486.0 230 60.00 1.028 0.041 1.7 04/15/09 28,337,703.6 266.8 1,840.02,048.3 188 60.00 0.863 0.028 2.0 04/15/09 29,779,733.7 269.51,840.02,152.6 201 60.00 1.468 0.051 1.3 04/15/09 32,291,749.7 271.0 1,840.02,351.7 218 60.00 1.714 0.064 1.5 04/15/09 34,676,777.2 273.7 1,840.02,563.1 238 60.00 1.098 0.045 1.6 04/15/09 36,225,998.0 274.1 1,840.02,677.6 248 60.00 1.266 0.054 1.8 04/15/09 36,424,624.5 274.6 1,840.02,692.3 248 60.00 1.351 0.058 2.1 04/15/09 36,634,181.5 275.1 1,840.02,667.9 248 60.00 1.542 0.066 2.4 04/15/09 36,673,679.8 275.2 1,840.02,710.7 248 60.00 1.773 0.077 2.4 04/15/09 36,318,315.4 274.2 1,840.02,684.4 248 60.00 2.026 0.087 2.6 04/15/09 36,622,034.5 275.0 1,840.02,706.8 248 60.00 2.026 0.088 2.2 04/15/09 36,749,937.6 275.7 1,840.02,716.3 248 60.00 2.195 0.095 1.6 04/15/09 36,992,906.4 274.7 1,840.02,734.3 249 60.00 1.857 0.081 1.1 04/15/09 34,610,129.7 271.3 1,840.02,482.9 232 60.00 1.392 0.055 4.7 04/15/09 29,727,986.9 265.9 1,840.02,116.5 196 60.00 0.964 0.033 4.7 04/15/09 25,271,101.5 263.1 1,840.0 1,771.7 161 60.00 4.183 0.119 1.0 04/15/09 24,248,954.5 262.2 1,840.0 1,673.7 155 60.00 4.249 0.114 0.9 04/15/09 23,590,573.6 262.0 1,840.0 1,692.4 154 60.00 0.870 0.024 1.2 04/15/09 24,430,818.4 264.51,840.0 1,712.8 160 60.00 0.801 0.022 1.3 04/14/09 27,083,918.3 265.51,840.0 1,913.5 178 60.00 1.060 0.032 1.8 04/14/09 25,708,413.9 264.3 1,840.0 1,788.4 166 60.00 1.166 0.033 2.4 04/14/09 26,284,925.8 266.7 1,840.0 1,842.8 175 60.00 1.602 0.047 1.9 04/14/09 33,093,123.0 273.1 1,840.02,374.1 225 60.00 2.088 0.079 1.3 04/14/09 36,503,456.1 274.7 1,840.02,638.5 245 60.00 1.640 0.069 1.0 04/14/09 35,693,949.4 273.8 1,840.02,580.1 238 60.00 1.122 0.046 1.1 04/14/09 32,293,896.7 269.1 1,840.02,334.3 211 60.00 0.863 0.032 1.4 04/14/09 33,621,352.0 273.6 1,840.02,430.2 228 60.00 0.950 0.037 2.1 04/14/09 36,561,903.3 274.6 1,840.02,642.8 245 60.00 1.209 0.051 2.3 04/14/09 35,444,700.1 274.7 1,840.02,562.1 236 60.00 1.813 0.074 2.5 04/14/09 36,409,143.6 275.6 1,840.02,631.7 244 60.00 1.986 0.084 2.3 04/14/09 36,669,957.8 275.51,840.02,670.5 248 60.00 2.142 0.091 1.9 04/14/09 36,612,214.6 274.3 1,840.02,666.3 248 60.00 1.971 0.084 1.9 04/14/09 35,867,431.6 273.7 1,840.02,612.1 243 60.00 1.628 0.068 2.0 04/14/09 37,105,758.5 276.1 1,840.02,682.1 251 60.00 1.640 0.070 2.5 04/14/09 37,318,892.6 275.8 1,840.02,717.8 255 60.00 1.714 0.074 04/14/09 37,615,314.4 275.0 1,840.02,718.9 255 60.00 2.158 0.094

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 C 02:00 C S S SC 03:00 S S SC 04:00 S S SC 05:00 C C 06:00 07:00 ST ST STC 08:00 C 2.2 4.7 04/17/09 34,981,043.5 277.1 1,840.02,604.6 240 60.00 1.844 0.077 2.6 04/17/09 35,892,246.0 276.7 1,840.02,652.9 244 60.00 3.968 0.168 2.5 04/17/09 35,585,976.1 275.51,840.02,649.6 243 60.00 2.179 0.092 4.7 04/17/09 34,775,840.4 273.6 1,840.02,589.3 238 60.00 2.095 0.087 4.7 04/17/09 31,665,235.2 269.51,840.02,306.0 213 60.00 4.027 0.148 4.7 04/17/09 26,447,088.1 265.2 1,840.0 1,882.9 172 60.00 4.119 0.124 1.6 04/17/09 23,595,195.9 265.1 1,840.0 1,641.4 153 60.00 4.216 0.111 1.6 04/17/09 25,780,599.2 265.7 1,840.0 1,835.5 175 60.00 1.402 0.041 2.2 04/17/09 25,664,500.5 266.1 1,840.0 1,827.2 175 60.00 1.402 0.041 2.3 04/16/09 27,613,734.9 266.9 1,840.0 1,981.0 189 60.00 1.914 0.061 1.9 04/16/09 24,448,039.7 264.7 1,840.0 1,767.2 164 60.00 1.986 0.056 2.3 04/16/09 25,818,694.1 269.4 1,840.0 1,852.2 179 60.00 1.653 0.049 2.7 04/16/09 31,880,938.0 273.9 1,840.02,339.1 220 60.00 1.956 0.073 2.5 04/16/09 34,527,225.8 275.8 1,840.02,589.5 236 60.00 2.246 0.093 1.9 04/16/09 31,103,091.2 269.3 1,840.02,265.1 212 60.00 2.142 0.078 1.4 04/16/09 29,867,112.6 270.1 1,840.02,175.1 202 60.00 1.628 0.057 2.0 04/16/09 29,292,926.8 269.2 1,840.02,117.4 196 60.00 1.209 0.041 2.5 04/16/09 29,594,226.5 272.3 1,840.02,139.1 203 60.00 1.727 0.059 2.2 04/16/09 33,063,071.2 273.6 1,840.02,461.8 229 60.00 2.095 0.082 2.1 04/16/09 34,868,378.2 275.6 1,840.02,577.2 240 60.00 1.857 0.077 2.7 04/16/09 34,692,786.6 275.7 1,840.02,545.4 238 60.00 1.786 0.073 2.8 04/16/09 34,591,431.8 275.3 1,840.02,537.9 236 60.00 2.296 0.093 1.8 04/16/09 35,329,400.1 275.4 1,840.02,611.3 244 60.00 2.364 0.099 1.8 04/16/09 33,819,858.8 274.3 1,840.02,499.7 230 60.00 1.520 0.061 1.2 04/16/09 34,820,485.2 275.8 1,840.02,554.7 237 60.00 1.531 0.063 1.9 04/16/09 32,304,766.8 274.7 1,840.02,352.6 218 60.00 1.028 0.039 1.8 04/16/09 35,336,789.7 277.1 1,840.02,592.7 240 60.00 1.616 0.067 1.4 04/16/09 31,243,042.8 270.8 1,840.02,292.3 210 60.00 1.531 0.056 1.6 04/16/09 25,996,432.6 265.8 1,840.0 1,850.8 172 60.00 1.227 0.036 1.4 04/16/09 24,302,289.9 263.8 1,840.0 1,730.2 159 60.00 1.402 0.039 1.8 04/16/09 23,013,290.5 263.2 1,840.0 1,625.9 151 60.00 1.236 0.032 1.4 04/16/09 23,173,128.3 262.8 1,840.0 1,675.0 152 60.00 1.554 0.042 0.8 04/16/09 22,727,901.6 262.6 1,840.0 1,642.8 151 60.00 1.209 0.032 1.2 04/15/09 24,417,683.0 264.9 1,840.0 1,765.0 162 60.00 0.691 0.019 1.7 04/15/09 26,976,845.0 268.1 1,840.0 1,906.0 182 60.00 1.060 0.032 1.5 04/15/09 29,307,266.1 269.2 1,840.02,070.6 197 60.00 1.501 0.050 04/15/09 30,449,603.3 268.6 1,840.02,184.5 203 60.00 1.305 0.046

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 1.5 1.3 04/18/09 30,097,592.4 269.7 1,840.02,110.1 200 60.00 1.335 0.045 1.0 04/18/09 32,419,973.3 273.4 1,840.02,308.2 222 60.00 1.139 0.042 1.0 04/18/09 31,613,209.7 271.8 1,840.02,182.0 215 60.00 0.904 0.032 1.0 04/18/09 35,422,223.3 273.2 1,840.02,464.1 239 60.00 0.897 0.035 1.3 04/18/09 32,955,856.6 272.1 1,840.02,274.7 220 60.00 0.904 0.033 1.6 04/18/09 33,195,976.5 273.6 1,840.02,291.2 221 60.00 1.175 0.043 1.8 04/18/09 35,020,921.9 274.4 1,840.02,455.3 232 60.00 1.424 0.056 1.8 04/18/09 33,638,011.9 273.1 1,840.02,376.6 225 60.00 1.590 0.060 1.7 04/18/09 32,877,026.9 271.51,840.02,340.7 220 60.00 1.578 0.059 1.8 04/18/09 34,306,845.6 274.8 1,840.02,442.5 229 60.00 1.490 0.058 1.7 04/18/09 35,220,929.3 273.4 1,840.02,507.6 232 60.00 1.578 0.063 1.9 04/18/09 34,613,464.7 274.4 1,840.02,464.3 231 60.00 1.490 0.059 1.4 04/18/09 36,087,724.8 274.9 1,840.02,608.5 243 60.00 1.640 0.068 1.1 04/18/09 36,094,889.4 274.3 1,840.02,569.8 240 60.00 1.227 0.050 0.7 04/18/09 35,167,133.8 272.3 1,840.02,427.3 231 60.00 0.994 0.039 0.9 04/18/09 31,685,198.2 265.9 1,840.02,187.0 203 60.00 0.633 0.022 0.9 04/18/09 24,397,901.6 263.2 1,840.0 1,697.3 160 60.00 0.807 0.022 0.6 04/18/09 26,583,796.7 263.51,840.0 1,878.2 177 60.00 0.795 0.024 0.6 04/18/09 25,018,023.7 263.0 1,840.0 1,740.4 162 60.00 0.538 0.015 0.9 04/18/09 23,993,645.1 262.7 1,840.0 1,643.1 155 60.00 0.547 0.014 0.7 04/18/09 23,521,940.7 262.3 1,840.0 1,623.5 151 60.00 0.814 0.021 1.2 04/18/09 23,789,763.7 263.3 1,840.0 1,642.0 151 60.00 0.633 0.017 1.1 04/17/09 25,133,856.0 264.4 1,840.0 1,734.8 164 60.00 1.085 0.030 1.9 04/17/09 26,131,097.7 266.3 1,840.0 1,803.6 173 60.00 0.994 0.029 1.9 04/17/09 29,457,067.6 270.7 1,840.02,081.2 199 60.00 1.678 0.056 1.8 04/17/09 33,269,089.2 273.2 1,840.02,404.8 228 60.00 1.640 0.063 1.5 04/17/09 34,250,188.6 274.0 1,840.02,475.7 235 60.00 1.554 0.062 2.3 04/17/09 32,923,873.9 270.8 1,840.02,379.8 221 60.00 1.295 0.049 1.8 04/17/09 30,222,566.7 269.3 1,840.02,135.3 200 60.00 2.031 0.069 1.6 04/17/09 30,801,226.2 270.0 1,840.02,159.4 202 60.00 1.602 0.055 2.1 04/17/09 30,474,327.4 272.4 1,840.02,219.3 209 60.00 1.371 0.049 1.8 04/17/09 33,997,612.7 274.3 1,840.02,494.4 232 60.00 1.786 0.071 0.6 04/17/09 34,373,868.2 273.4 1,840.02,540.7 236 60.00 1.520 0.062 1.5 04/17/09 33,830,056.8 274.1 1,840.02,482.1 233 60.00 0.510 0.020 1.9 04/17/09 35,361,715.8 275.6 1,840.02,613.7 242 60.00 1.266 0.053 2.0 04/17/09 36,030,512.3 276.3 1,840.02,663.2 247 60.00 1.604 0.068 04/17/09 35,813,989.1 275.0 1,840.02,647.1 244 60.00 1.688 0.071

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 S S S 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 3.8 3.9 04/20/09 36,450,446.3 278.2 1,840.02,674.3 250 60.00 3.232 0.138 3.3 04/20/09 36,317,074.8 277.1 1,840.02,664.6 250 60.00 3.317 0.141 2.9 04/20/09 35,874,576.1 276.3 1,840.02,632.1 247 60.00 2.807 0.118 3.3 04/20/09 35,430,546.2 275.1 1,840.02,580.3 242 60.00 2.485 0.103 2.3 04/20/09 35,713,289.1 276.0 1,840.02,600.8 243 60.00 2.828 0.118 1.2 04/20/09 34,799,067.0 270.0 1,840.02,515.4 235 60.00 1.986 0.080 1.4 04/20/09 26,995,882.5 262.8 1,840.0 1,907.3 176 60.00 1.060 0.032 2.1 04/20/09 24,562,608.5 266.0 1,840.0 1,708.7 163 60.00 1.256 0.034 2.6 04/20/09 29,470,892.0 269.0 1,840.02,050.2 198 60.00 1.884 0.062 2.1 04/20/09 30,787,106.9 269.1 1,840.02,208.6 211 60.00 2.262 0.080 2.3 04/20/09 30,606,667.9 269.7 1,840.02,195.7 209 60.00 1.827 0.064 2.2 04/19/09 30,928,798.2 271.1 1,840.02,218.8 210 60.00 2.001 0.071 2.7 04/19/09 31,464,400.9 271.51,840.02,240.1 212 60.00 1.928 0.069 2.5 04/19/09 33,499,297.6 272.9 1,840.02,439.6 228 60.00 2.313 0.090 2.2 04/19/09 34,043,994.1 274.3 1,840.02,460.8 234 60.00 2.158 0.085 2.0 04/19/09 35,710,689.8 275.6 1,840.02,581.3 243 60.00 1.899 0.078 1.7 04/19/09 35,398,987.6 275.0 1,840.02,558.7 241 60.00 1.727 0.071 2.3 04/19/09 32,880,549.5 273.6 1,840.02,376.7 225 60.00 1.468 0.056 2.3 04/19/09 34,218,732.7 274.2 1,840.02,492.0 236 60.00 1.971 0.079 1.9 04/19/09 34,637,218.1 275.1 1,840.02,503.7 237 60.00 1.986 0.079 1.5 04/19/09 34,486,549.9 274.0 1,840.02,455.3 235 60.00 1.665 0.065 1.6 04/19/09 34,047,480.7 272.3 1,840.02,424.0 231 60.00 1.315 0.051 1.5 04/19/09 32,764,438.0 272.6 1,840.02,332.7 226 60.00 1.402 0.052 1.2 04/19/09 33,611,160.4 273.9 1,840.02,411.2 231 60.00 1.305 0.050 1.2 04/19/09 34,856,436.8 273.9 1,840.02,481.6 237 60.00 1.052 0.042 0.9 04/19/09 34,931,675.2 272.7 1,840.02,487.0 236 60.00 1.052 0.042 1.3 04/19/09 32,412,040.8 272.2 1,840.02,342.8 227 60.00 0.777 0.029 1.2 04/19/09 35,108,365.4 271.3 1,840.02,404.1 229 60.00 1.185 0.046 1.7 04/19/09 28,656,905.0 263.8 1,840.0 1,962.4 179 60.00 1.093 0.034 0.7 04/19/09 24,001,811.8 260.7 1,840.0 1,617.5 152 60.00 1.574 0.041 4.7 04/19/09 23,950,181.0 261.3 1,840.0 1,640.1 156 60.00 0.638 0.017 4.7 04/19/09 23,933,636.7 262.51,840.0 1,652.0 156 60.00 4.249 0.112 4.7 04/19/09 23,934,628.9 263.0 1,840.0 1,613.0 152 60.00 4.352 0.112 4.7 04/19/09 24,365,546.0 264.2 1,840.0 1,681.8 158 60.00 4.249 0.114 1.3 04/19/09 27,643,143.8 267.0 1,840.0 1,953.0 188 60.00 4.151 0.130 1.6 04/18/09 30,368,204.6 270.0 1,840.02,162.1 207 60.00 1.139 0.039 04/18/09 29,689,458.0 268.7 1,840.02,129.9 202 60.00 1.392 0.047

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C S S S 03:00 S S S 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 * * C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 2.0 2.1 04/21/09 25,060,004.0 266.7 1,840.0 1,770.5 169 60.00 1.766 0.050 3.0 04/21/09 26,267,391.5 266.6 1,840.0 1,884.4 176 60.00 1.827 0.055 3.0 04/21/09 31,168,732.1 274.2 1,840.02,236.0 218 60.00 2.609 0.093 3.1 04/21/09 34,882,360.4 276.2 1,840.02,578.2 240 60.00 2.533 0.104 2.8 04/21/09 34,857,075.2 275.6 1,840.02,557.4 239 60.00 2.637 0.108 3.2 04/21/09 31,106,044.9 270.51,840.02,248.4 212 60.00 2.417 0.087 3.3 04/21/09 30,576,311.3 270.1 1,840.02,210.1 211 60.00 2.762 0.098 3.1 04/21/09 30,491,703.5 270.2 1,840.02,204.0 210 60.00 2.849 0.100 3.1 04/21/09 31,963,964.2 273.4 1,840.02,310.4 221 60.00 2.676 0.099 3.0 04/21/09 33,625,386.6 274.51,840.02,430.5 231 60.00 2.676 0.104 3.1 04/21/09 34,202,304.8 274.7 1,840.02,416.4 234 60.00 2.650 0.102 2.0 04/21/09 34,403,836.5 275.7 1,840.02,468.1 236 60.00 2.696 0.106 1.7 04/21/09 34,922,988.0 276.4 1,840.02,505.3 240 60.00 1.740 0.070 1.7 04/21/09 35,219,134.3 276.1 1,840.02,526.6 242 60.00 1.479 0.060 1.8 04/21/09 33,957,530.9 276.4 1,840.02,417.7 234 60.00 1.490 0.058 2.3 04/21/09 34,438,354.0 275.51,840.02,470.6 239 60.00 1.566 0.062 2.4 04/21/09 33,918,549.8 274.51,840.02,433.3 236 60.00 2.001 0.078 1.3 04/21/09 34,555,362.0 273.2 1,840.02,516.5 240 60.00 2.056 0.083 0.6 04/21/09 30,137,877.1 266.7 1,840.02,162.1 206 60.00 1.131 0.039 4.7 04/21/09 27,382,807.0 263.4 1,840.0 1,890.0 179 60.00 0.542 0.016 4.7 04/21/09 24,989,420.8 262.7 1,840.0 1,670.5 155 60.00 4.387 0.117 0.8 04/21/09 24,244,505.7 263.1 1,840.0 1,607.5 151 60.00 4.423 0.114 1.4 04/21/09 23,846,277.2 263.0 1,840.0 1,620.0 152 60.00 0.735 0.019 1.1 04/21/09 23,405,085.3 262.51,840.0 1,640.9 153 60.00 1.246 0.033 1.6 04/20/09 23,911,601.2 264.1 1,840.0 1,650.4 154 60.00 0.994 0.026 1.1 04/20/09 26,279,437.0 268.8 1,840.0 1,828.1 177 60.00 1.435 0.042 2.1 04/20/09 28,888,716.4 270.6 1,840.0 1,994.0 193 60.00 0.994 0.032 2.6 04/20/09 33,321,298.2 274.51,840.02,354.2 230 60.00 1.855 0.070 2.4 04/20/09 34,622,988.4 273.1 1,840.02,483.8 238 60.00 2.262 0.090 2.5 04/20/09 28,142,651.7 266.8 1,840.0 1,973.1 185 60.00 2.136 0.067 2.6 04/20/09 30,654,685.0 271.0 1,840.02,199.2 213 60.00 2.175 0.076 2.3 04/20/09 31,178,481.7 271.6 1,840.02,219.7 212 60.00 2.279 0.081 2.7 04/20/09 30,745,794.8 270.1 1,840.02,205.7 207 60.00 2.001 0.071 3.5 04/20/09 29,203,859.5 271.1 1,840.02,063.3 197 60.00 2.385 0.079 3.4 04/20/09 35,018,297.2 276.1 1,840.02,512.2 239 60.00 3.044 0.122 3.0 04/20/09 36,263,098.6 277.4 1,840.02,601.5 247 60.00 2.957 0.123 04/20/09 36,449,842.4 278.0 1,840.02,654.5 249 60.00 2.571 0.109

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C S S S 03:00 S S S 04:00 C 05:00 C C 06:00 07:00 08:00 C 09:00 C 10:00 C 11:00 C 12:00 C 2.9 2.5 04/23/09 33,118,786.6 273.9 1,840.02,447.9 229 60.00 2.448 0.096 2.1 04/23/09 33,556,517.6 273.6 1,840.02,498.5 233 60.00 2.095 0.084 2.0 04/23/09 33,969,416.0 275.0 1,840.02,529.2 235 60.00 1.760 0.071 2.6 04/23/09 33,359,313.6 273.6 1,840.02,483.8 231 60.00 1.676 0.067 2.9 04/23/09 32,713,947.1 272.6 1,840.02,435.8 228 60.00 2.179 0.085 2.5 04/23/09 33,115,462.5 272.7 1,840.02,483.6 231 60.00 2.413 0.096 2.3 04/23/09 33,551,431.5 271.3 1,840.02,516.3 235 60.00 2.080 0.084 2.9 04/23/09 29,663,260.6 266.4 1,840.02,144.1 201 60.00 1.986 0.068 4.7 04/23/09 24,838,244.2 263.3 1,840.0 1,781.9 164 60.00 2.522 0.072 4.7 04/23/09 23,259,478.6 262.4 1,840.0 1,655.9 152 60.00 4.119 0.109 2.4 04/23/09 23,100,308.1 262.51,840.0 1,619.5 152 60.00 4.183 0.108 1.7 04/23/09 23,359,682.9 262.3 1,840.0 1,650.4 153 60.00 2.120 0.056 1.0 04/23/09 23,278,935.5 262.3 1,840.0 1,644.7 151 60.00 1.501 0.039 1.2 04/22/09 23,473,445.5 262.9 1,840.0 1,645.7 155 60.00 0.890 0.023 1.1 04/22/09 23,836,874.0 263.1 1,840.0 1,658.2 159 60.00 1.076 0.029 1.6 04/22/09 23,992,800.8 264.2 1,840.0 1,656.0 158 60.00 0.994 0.026 1.9 04/22/09 26,741,752.9 269.4 1,840.0 1,874.8 185 60.00 1.424 0.043 1.4 04/22/09 33,701,779.3 272.6 1,840.02,436.1 229 60.00 1.640 0.064 1.7 04/22/09 27,930,882.0 267.1 1,840.02,003.7 186 60.00 1.218 0.039 2.1 04/22/09 27,117,660.0 269.9 1,840.0 1,945.4 183 60.00 1.479 0.046 2.3 04/22/09 29,886,128.6 270.6 1,840.02,176.5 205 60.00 1.799 0.063 2.4 04/22/09 32,897,183.2 273.7 1,840.02,431.5 228 60.00 1.942 0.075 2.1 04/22/09 34,225,557.3 274.1 1,840.02,529.7 237 60.00 2.026 0.082 2.5 04/22/09 34,028,536.8 273.3 1,840.02,515.2 235 60.00 1.773 0.071 2.6 04/22/09 34,411,300.7 276.4 1,840.02,468.6 237 60.00 2.175 0.086 2.9 04/22/09 35,897,428.5 276.3 1,840.02,653.3 245 60.00 2.195 0.093 3.1 04/22/09 35,675,376.9 277.3 1,840.02,656.2 244 60.00 2.430 0.103 3.2 04/22/09 35,534,337.9 276.3 1,840.02,626.4 245 60.00 2.617 0.110 2.7 04/22/09 35,871,459.6 275.8 1,840.02,670.8 248 60.00 2.682 0.115 2.2 04/22/09 35,788,596.0 274.6 1,840.02,645.3 247 60.00 2.279 0.096 1.8 04/22/09 34,777,244.0 272.7 1,840.02,589.4 239 60.00 1.844 0.076 2.1 04/22/09 29,528,269.0 267.8 1,840.02,150.4 200 60.00 1.542 0.053 1.6 04/22/09 25,100,857.4 266.3 1,840.0 1,800.7 169 60.00 1.827 0.053 1.5 04/22/09 27,408,670.2 265.0 1,840.0 1,966.3 186 60.00 1.392 0.044 1.7 04/22/09 24,151,727.6 262.51,840.0 1,732.6 163 60.00 1.305 0.036 1.9 04/22/09 23,585,140.1 263.0 1,840.0 1,666.3 156 60.00 1.501 0.040 04/22/09 23,983,951.7 264.4 1,840.0 1,681.5 159 60.00 1.691 0.045

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 C 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 0.6 0.6 04/25/09 7,506,783.0 245.4 1,840.0 0.0 0 0.00 0.000 0.2 04/25/09 7,491,577.2 235.1 1,840.0 0.0 0 0.00 0.000 0.2 04/24/09 7,230,734.1 212.0 1,840.0 0.0 0 0.00 0.000 0.4 04/24/09 3,806,556.5 197.9 1,840.0 0.0 0 0.00 0.000 0.0 04/24/09 2,759,871.1 203.7 1,840.0 0.0 0 0.00 0.000 0.6 04/24/09 24,622,444.9 220.4 1,840.0 13.4 0 55.00 0.000 0.000 1.9 04/24/09 23,358,954.9 237.4 1,840.0 101.6 12 49.00 8.611 0.011 2.8 04/24/09 25,342,165.4 247.4 1,840.0 550.9 43 60.00 5.454 0.048 3.8 04/24/09 23,848,163.4 250.7 1,840.0 855.4 77 60.00 4.871 0.067 4.2 04/24/09 25,491,178.1 257.7 1,840.0 1,039.0 97 60.00 5.817 0.097 4.3 04/24/09 24,696,985.7 260.0 1,840.0 1,208.0 120 60.00 5.358 0.103 4.6 04/24/09 25,188,706.3 262.3 1,840.0 1,259.5 125 60.00 5.366 0.108 4.9 04/24/09 28,209,320.7 265.8 1,840.0 1,579.1 147 60.00 5.128 0.129 4.8 04/24/09 31,224,973.7 269.7 1,840.02,019.4 191 60.00 4.728 0.153 4.8 04/24/09 31,654,776.8 271.3 1,840.02,030.0 194 60.00 4.670 0.152 4.7 04/24/09 33,083,442.6 272.1 1,840.02,139.6 205 60.00 4.631 0.158 4.6 04/24/09 32,786,006.3 272.1 1,840.02,334.2 220 60.00 4.119 0.154 4.5 04/24/09 30,970,081.8 272.3 1,840.02,188.1 208 60.00 4.063 0.142 4.0 04/24/09 32,674,382.9 271.4 1,840.02,344.0 221 60.00 3.914 0.147 3.8 04/24/09 31,813,107.1 268.8 1,840.02,213.1 203 60.00 3.588 0.127 4.1 04/24/09 25,936,348.2 263.4 1,840.0 1,762.0 164 60.00 3.490 0.098 3.6 04/24/09 23,853,459.3 262.4 1,840.0 1,607.5 153 60.00 3.796 0.098 3.4 04/24/09 23,657,389.4 262.51,840.0 1,632.8 155 60.00 3.255 0.085 3.4 04/24/09 24,098,420.5 262.6 1,840.0 1,650.2 154 60.00 3.098 0.082 3.3 04/24/09 23,436,294.0 262.8 1,840.0 1,604.9 152 60.00 3.098 0.080 3.2 04/24/09 23,632,521.3 262.7 1,840.0 1,644.0 154 60.00 2.960 0.078 2.6 04/23/09 23,429,227.6 263.2 1,840.0 1,642.6 153 60.00 2.848 0.075 3.4 04/23/09 22,913,406.4 264.3 1,840.0 1,643.8 153 60.00 2.262 0.059 4.5 04/23/09 25,487,954.7 269.4 1,840.0 1,814.6 174 60.00 2.980 0.086 4.2 04/23/09 31,590,970.1 273.4 1,840.02,300.6 218 60.00 3.856 0.142 3.2 04/23/09 33,152,620.1 271.8 1,840.02,432.4 227 60.00 3.572 0.139 3.2 04/23/09 29,873,676.7 270.8 1,840.02,175.6 205 60.00 2.742 0.095 3.5 04/23/09 31,193,181.9 270.6 1,840.02,288.6 212 60.00 2.722 0.100 3.3 04/23/09 30,202,548.9 270.9 1,840.02,216.0 206 60.00 2.977 0.105 3.1 04/23/09 31,375,222.3 272.1 1,840.02,284.9 216 60.00 2.828 0.103 3.0 04/23/09 33,413,174.0 273.6 1,840.02,451.5 230 60.00 2.637 0.103 04/23/09 33,176,816.7 271.9 1,840.02,452.2 230 60.00 2.533 0.099

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 0.0 0.0 04/26/09 8,088,074.5 68.9 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,290,727.0 68.7 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,321,692.8 68.2 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,223,740.4 68.2 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,438,180.4 68.2 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,285,236.0 67.9 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,137,414.5 67.9 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,220,285.8 68.1 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,367,526.8 68.4 1,840.0 0.0 0 0.00 0.000 2.4 04/26/09 8,445,555.6 68.9 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,417,288.4 69.51,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,444,493.9 70.3 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 12,550,507.9 71.51,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,636,525.8 72.9 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,759,837.4 74.6 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,024,930.8 76.51,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,274,073.7 78.7 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,831,293.7 81.7 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,881,424.3 84.9 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,938,924.8 87.7 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,854,202.2 91.1 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,371,969.3 94.8 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 8,622,807.2 99.0 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 8,529,163.5 103.6 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 8,586,176.8 108.6 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 8,992,674.8 114.9 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,400,696.7 122.3 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,467,753.0 130.8 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,405,541.6 139.4 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,502,841.9 146.9 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 9,444,222.5 151.6 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 8,957,395.9 158.4 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 8,483,210.4 170.8 1,840.0 0.0 0 0.00 0.000 2.4 04/25/09 8,413,212.0 187.1 1,840.0 0.0 0 0.00 0.000 0.0 04/25/09 8,304,053.4 207.1 1,840.0 0.0 0 0.00 0.000 0.2 04/25/09 7,988,327.2 226.8 1,840.0 0.0 0 0.00 0.000 04/25/09 11,909,283.3 242.1 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 0.0 0.0 04/28/09 8,741,950.3 68.9 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 12,722,266.8 70.3 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 8,978,190.8 71.51,840.0 0.0 0 0.00 0.000 0.0 04/28/09 9,309,117.7 72.9 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,334,823.6 74.3 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,537,238.9 75.4 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,893,054.4 76.3 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,892,551.1 77.1 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,757,921.6 77.9 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,545,216.1 78.4 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,451,212.4 78.8 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,228,315.3 79.2 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,265,014.8 79.7 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,395,622.1 79.3 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,289,262.3 79.0 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,220,371.0 78.3 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,405,855.8 77.0 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 9,018,690.2 76.4 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 8,758,367.1 76.4 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 8,114,491.4 75.2 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 8,108,851.4 74.4 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 7,837,517.1 73.9 1,840.0 0.0 0 0.00 0.000 2.3 04/27/09 7,692,738.9 73.7 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 7,769,704.3 73.7 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 8,034,260.3 72.9 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 12,204,455.5 72.8 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 7,638,706.5 72.7 1,840.0 0.0 0 0.00 0.000 0.0 04/27/09 7,806,514.2 72.4 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,284,055.1 72.2 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,247,891.0 72.0 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,940,809.3 72.1 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,677,937.2 72.0 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 8,393,393.6 71.6 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 7,667,446.1 71.0 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 7,371,596.5 70.0 1,840.0 0.0 0 0.00 0.000 0.0 04/26/09 7,632,312.8 69.3 1,840.0 0.0 0 0.00 0.000 04/26/09 7,849,337.3 69.0 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F FC 12:00 F F F F F F F F FC 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 0.0 0.0 04/29/09 9,883,641.6 69.51,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,896,619.8 69.1 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,893,353.4 68.6 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,821,688.1 67.9 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,854,783.7 67.2 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,898,443.3 66.51,840.0 0.0 0 0.00 0.000 0.0 04/29/09 10,180,755.0 65.7 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 10,098,182.1 65.0 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 10,236,458.8 64.6 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 10,224,085.2 64.6 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 10,198,554.3 64.9 1,840.0 0.0 0 0.00 0.000 2.3 04/29/09 10,094,129.7 64.9 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 10,025,085.7 64.8 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 10,014,481.3 64.7 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 13,485,538.9 64.51,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,969,050.1 64.7 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,815,240.8 64.51,840.0 0.0 0 0.00 0.000 0.0 04/28/09 9,866,732.8 64.2 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 9,840,786.0 63.8 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 9,880,718.8 63.4 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 9,888,559.8 63.1 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 9,882,205.4 62.9 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,017,108.9 62.7 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,044,641.5 62.6 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,046,373.8 62.51,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,102,307.3 62.1 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,300,867.7 61.8 1,840.0 0.0 0 0.00 0.000 1.3 04/28/09 10,349,003.3 61.8 1,840.0 0.0 0 0.00 0.000 2.1 04/28/09 10,274,799.9 62.0 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,284,177.0 62.2 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,328,547.3 62.2 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,301,835.6 62.6 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,309,919.5 63.1 1,840.0 0.0 0 0.00 0.000 0.0 04/28/09 10,251,359.6 63.8 1,840.0 0.0 0 0.00 0.000 0.1 04/28/09 10,303,731.7 64.7 1,840.0 0.0 0 0.00 0.000 2.4 04/28/09 9,808,175.6 66.2 1,840.0 0.0 0 0.00 0.000 04/28/09 8,933,970.3 67.7 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 0.0 2.4 05/01/09 9,476,008.9 74.51,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,662,375.1 74.9 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,584,006.4 75.3 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 12,567,147.2 75.6 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,631,245.1 75.7 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,824,012.5 75.6 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,045,038.4 75.0 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,677,026.1 75.4 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,631,708.9 75.2 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,760,207.5 74.51,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,753,001.1 73.8 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,695,846.8 72.8 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,731,159.3 72.2 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,834,562.8 71.51,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,899,762.2 70.8 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,882,283.2 70.1 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 10,075,792.5 69.51,840.0 0.0 0 0.00 0.000 0.0 04/30/09 10,143,347.2 69.1 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 10,109,630.7 69.3 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 10,107,589.6 69.6 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 10,017,091.5 69.8 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,937,263.8 70.0 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,973,508.3 70.2 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 9,849,929.3 70.3 1,840.0 0.0 0 0.00 0.000 2.3 04/30/09 9,422,712.4 70.6 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 8,552,546.4 70.9 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 8,569,225.5 71.0 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 12,461,848.6 70.8 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 8,470,736.4 70.4 1,840.0 0.0 0 0.00 0.000 0.0 04/30/09 8,428,280.4 70.1 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 8,516,396.9 69.9 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,199,409.4 69.7 1,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,387,873.0 69.51,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,456,653.5 69.51,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,537,643.4 69.51,840.0 0.0 0 0.00 0.000 0.0 04/29/09 9,644,855.1 69.6 1,840.0 0.0 0 0.00 0.000 04/29/09 9,669,395.2 69.6 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 0.0 0.0 05/02/09 287,617.5 72.3 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 235,112.3 72.3 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 234,981.9 72.4 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 240,744.6 72.4 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 1,685,298.2 72.7 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,236,337.2 72.6 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,220,841.7 72.1 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,297,784.1 71.6 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,387,091.9 71.3 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,404,793.9 70.9 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,495,079.3 70.6 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,569,616.2 70.6 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,683,557.5 70.9 1,840.0 0.0 0 0.00 0.000 2.4 05/02/09 8,867,826.1 71.6 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,899,818.0 72.4 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,941,840.7 73.1 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 12,734,624.7 73.8 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,695,258.7 74.4 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 8,520,744.5 74.9 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,495,773.2 75.2 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,537,381.1 75.4 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,684,023.9 75.4 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 8,978,544.9 75.51,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,149,948.7 75.3 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,072,993.8 74.9 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,128,949.6 74.8 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,181,057.6 74.6 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,192,388.5 74.3 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,192,762.7 73.9 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,138,515.3 73.51,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,160,337.7 73.4 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,187,486.8 73.3 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,277,925.9 73.3 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,350,765.4 73.3 1,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,553,369.6 73.51,840.0 0.0 0 0.00 0.000 0.0 05/01/09 9,809,553.4 73.8 1,840.0 0.0 0 0.00 0.000 05/01/09 9,820,140.1 74.2 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 0.0 0.0 05/04/09 397,181.9 68.7 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 325,000.7 68.3 1,840.0 0.0 0 0.00 0.000 2.4 05/04/09 295,108.3 68.2 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 271,349.3 68.4 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 270,616.0 68.6 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 7,032,742.9 68.7 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 280,670.7 68.8 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 290,669.3 68.8 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 306,184.4 68.9 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 347,240.4 69.0 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 429,293.8 69.1 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 477,065.2 69.3 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 491,413.6 69.51,840.0 0.0 0 0.00 0.000 0.0 05/03/09 459,757.3 69.7 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 329,782.2 69.9 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 236,973.6 70.1 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 278,218.3 70.4 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 325,709.2 70.7 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 354,576.1 70.8 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 345,111.8 71.0 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 395,704.1 71.3 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 508,668.1 71.3 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 493,415.2 71.0 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 358,638.5 70.1 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 283,159.4 69.4 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 263,173.7 68.9 1,840.0 0.0 0 0.00 0.000 2.4 05/03/09 318,515.0 69.0 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 337,342.6 69.4 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 344,212.9 69.7 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 7,066,805.8 70.0 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 298,175.7 70.4 1,840.0 0.0 0 0.00 0.000 0.0 05/03/09 280,585.8 70.8 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 295,044.3 71.2 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 347,273.9 71.6 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 454,356.3 71.9 1,840.0 0.0 0 0.00 0.000 0.0 05/02/09 462,105.0 72.1 1,840.0 0.0 0 0.00 0.000 05/02/09 406,543.3 72.2 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F FC 12:00 F F F F F F F F FC 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 0.0 0.0 05/05/09 6,911,752.6 76.0 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 6,774,708.4 76.0 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 8,138,202.9 76.0 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 9,588,679.1 75.7 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 9,671,681.3 75.2 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 9,031,071.2 74.2 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 8,869,831.1 72.51,840.0 0.0 0 0.00 0.000 1.2 05/05/09 3,555,077.9 69.4 1,840.0 0.0 0 0.00 0.000 2.0 05/05/09 522,499.3 68.51,840.0 0.0 0 0.00 0.000 0.0 05/05/09 507,233.8 68.7 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 515,173.3 68.6 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 510,617.2 68.4 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 489,547.9 68.1 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 452,051.4 67.7 1,840.0 0.0 0 0.00 0.000 0.1 05/05/09 426,456.9 67.6 1,840.0 0.0 0 0.00 0.000 2.3 05/05/09 410,405.6 67.6 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 398,731.9 67.6 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 379,779.5 67.8 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 7,059,318.0 68.1 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 338,783.1 68.51,840.0 0.0 0 0.00 0.000 0.0 05/05/09 308,225.8 68.8 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 305,669.5 69.2 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 375,785.9 69.8 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 466,229.9 70.51,840.0 0.0 0 0.00 0.000 0.0 05/04/09 469,163.2 70.9 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 477,458.7 71.2 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 440,385.3 71.2 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 409,712.3 71.0 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 403,649.2 70.9 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 425,955.0 70.4 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 422,748.5 70.1 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 474,491.9 70.1 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 519,714.2 69.9 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 570,523.5 70.1 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 552,171.1 70.0 1,840.0 0.0 0 0.00 0.000 0.0 05/04/09 443,714.0 69.7 1,840.0 0.0 0 0.00 0.000 05/04/09 409,905.8 69.3 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 0.0 0.0 05/07/09 5,754,622.6 77.8 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,816,478.3 77.3 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,889,206.8 77.0 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,913,983.0 76.8 1,840.0 0.0 0 0.00 0.000 2.3 05/07/09 5,973,243.8 76.6 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,956,717.8 76.51,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,902,008.8 76.51,840.0 0.0 0 0.00 0.000 0.0 05/07/09 10,811,673.6 76.51,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,976,533.0 76.4 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,030,940.4 76.4 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,091,215.7 76.4 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,215,506.5 76.3 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,514,288.5 76.2 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,891,546.2 76.2 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,918,550.8 76.1 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 7,036,662.5 75.51,840.0 0.0 0 0.00 0.000 0.0 05/06/09 7,218,822.8 75.6 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 7,126,040.7 75.51,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,984,204.6 75.1 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,890,015.5 74.6 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,825,004.1 74.3 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,887,909.1 74.0 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,906,642.4 73.9 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 7,022,173.2 73.8 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,980,582.6 73.8 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 7,004,603.9 74.0 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,900,577.4 74.2 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,450,203.8 74.51,840.0 0.0 0 0.00 0.000 2.3 05/06/09 6,333,689.8 74.8 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,449,792.8 75.1 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,776,876.2 75.4 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 11,369,108.5 75.7 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 6,746,672.1 75.9 1,840.0 0.0 0 0.00 0.000 0.0 05/06/09 7,077,760.6 76.0 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 7,040,942.8 76.1 1,840.0 0.0 0 0.00 0.000 0.0 05/05/09 6,968,481.3 76.0 1,840.0 0.0 0 0.00 0.000 05/05/09 6,945,366.3 76.0 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F F 05:00 FC F F F F F F F F 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 0.0 0.0 05/08/09 2,709,175.7 69.6 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 3,776,305.4 70.7 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 3,774,991.9 71.7 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 3,964,407.9 72.9 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 2,820,762.0 50.6 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 4,087,362.5 77.0 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 4,490,422.3 79.4 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 5,627,936.0 79.6 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 2,229,733.7 30.6 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,206,713.2 75.3 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,618,023.2 79.4 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,687,663.7 79.4 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 784,527.1 9.3 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 4,846,149.9 59.7 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,183,572.8 79.8 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,284,245.0 80.3 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,242,360.4 80.7 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 11,011,616.3 81.1 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,304,601.2 81.4 1,840.0 0.0 0 0.00 0.000 0.0 05/08/09 6,403,802.2 81.6 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,552,611.2 81.9 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,824,214.8 82.1 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,904,878.1 82.2 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,847,430.5 82.3 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,701,455.8 82.0 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,624,240.4 81.8 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,577,992.9 81.6 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 6,000,492.3 81.2 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,595,432.6 80.3 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,593,714.0 79.7 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,562,837.3 78.7 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,557,155.7 77.9 1,840.0 0.0 0 0.00 0.000 0.0 05/07/09 5,653,884.4 78.1 1,840.0 0.0 0 0.00 0.000 05/07/09 5,689,169.6 78.1 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 0.0 0.0 05/10/09 1,700,593.1 81.3 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,925,799.8 72.3 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,622,810.8 57.2 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,589,021.8 57.1 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,447,714.6 57.0 1,840.0 0.0 0 0.00 0.000 0.1 05/10/09 1,242,667.7 57.1 1,840.0 0.0 0 0.00 0.000 2.3 05/10/09 1,244,741.5 57.1 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,204,577.6 57.3 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,211,584.2 57.6 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 7,639,035.4 57.8 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,259,631.2 58.1 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,279,207.6 58.4 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,294,719.9 58.7 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,316,118.6 59.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,407,018.1 59.3 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,555,725.7 59.6 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,562,714.8 57.8 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 836,309.6 30.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,803,552.2 60.2 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,697,785.3 60.51,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,553,976.5 60.9 1,840.0 0.0 0 0.00 0.000 0.1 05/09/09 1,450,980.1 61.2 1,840.0 0.0 0 0.00 0.000 2.3 05/09/09 1,610,599.1 62.0 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,700,724.7 63.2 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,641,061.7 64.3 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 8,239,928.9 65.51,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,919,807.7 66.7 1,840.0 0.0 0 0.00 0.000 0.0 05/09/09 1,887,438.7 67.7 1,840.0 0.0 0 0.00 0.000 05/08/09 1,928,851.0 68.7 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 0.0 0.0 05/12/09 1,235,647.1 85.9 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 528,228.8 72.3 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 638,900.8 74.2 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 647,068.3 76.4 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 624,531.6 79.7 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 327,082.2 84.4 1,840.0 0.0 0 0.00 0.000 0.1 05/11/09 498,388.0 95.7 1,840.0 0.0 0 0.00 0.000 0.1 05/11/09 1,398,994.8 107.3 1,840.0 0.0 0 0.00 0.000 0.1 05/11/09 1,454,838.4 107.1 1,840.0 0.0 0 0.00 0.000 0.1 05/11/09 1,444,769.1 107.4 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,283,437.0 106.3 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,358,449.9 105.6 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,260,521.3 101.3 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 0.0 0.0 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 158,040.9 13.0 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,348,538.2 103.7 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,291,020.2 102.51,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,071,039.0 84.0 1,840.0 0.0 0 0.00 0.000 0.1 05/11/09 968,491.2 70.3 1,840.0 0.0 0 0.00 0.000 2.4 05/11/09 1,285,523.1 94.3 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,239,339.8 92.0 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,250,413.6 92.1 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 7,651,295.5 91.2 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,178,764.5 90.2 1,840.0 0.0 0 0.00 0.000 0.0 05/11/09 1,260,712.1 89.4 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,207,639.1 88.8 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,202,085.1 87.6 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,234,908.9 84.9 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,617,620.6 84.0 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,631,475.2 85.0 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,673,885.6 84.0 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,618,193.7 84.0 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,691,723.5 83.3 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,758,375.8 84.4 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,658,756.0 83.7 1,840.0 0.0 0 0.00 0.000 0.0 05/10/09 1,709,681.5 84.0 1,840.0 0.0 0 0.00 0.000 05/10/09 1,725,621.6 83.51,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F FC 12:00 F F F F F F F F FC 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F FC 16:00 F F F F F F F F FC 17:00 F F F F F F F F FC 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 0.1 0.2 05/13/09 1,560,135.6 98.3 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,668,719.8 100.9 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,559,002.5 102.8 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,459,536.0 103.0 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,461,590.3 102.3 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,504,909.6 101.4 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,472,146.0 99.8 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,491,800.9 96.2 1,840.0 0.0 0 0.00 0.000 2.4 05/13/09 1,391,127.1 94.0 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,492,512.6 94.0 1,840.0 0.0 0 0.00 0.000 0.0 05/13/09 1,493,342.7 96.2 1,840.0 0.0 0 0.00 0.000 0.0 05/13/09 7,725,677.9 94.7 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,348,068.7 95.0 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,397,660.3 95.7 1,840.0 0.0 0 0.00 0.000 0.0 05/12/09 1,405,400.2 96.51,840.0 0.0 0 0.00 0.000 0.0 05/12/09 1,300,783.2 96.0 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,432,005.1 97.2 1,840.0 0.0 0 0.00 0.000 0.0 05/12/09 1,284,483.1 97.6 1,840.0 0.0 0 0.00 0.000 0.0 05/12/09 1,239,049.9 97.4 1,840.0 0.0 0 0.00 0.000 0.4 05/12/09 1,249,889.7 97.51,840.0 0.0 0 0.00 0.000 2.3 05/12/09 1,359,795.9 98.7 1,840.0 0.0 0 0.00 0.000 2.3 05/12/09 1,307,753.6 98.8 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,335,553.9 99.3 1,840.0 0.0 0 0.00 0.000 0.2 05/12/09 1,465,790.8 101.51,840.0 0.0 0 0.00 0.000 1.4 05/12/09 1,437,863.7 103.0 1,840.0 0.0 0 0.00 0.000 2.2 05/12/09 1,439,236.5 105.0 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,413,492.3 107.1 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,384,302.3 108.2 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,249,963.7 109.2 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,305,241.5 107.6 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,295,850.4 105.1 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,327,542.4 101.8 1,840.0 0.0 0 0.00 0.000 2.3 05/12/09 1,252,345.1 97.1 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,254,350.3 95.6 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 1,216,211.0 95.3 1,840.0 0.0 0 0.00 0.000 0.1 05/12/09 7,677,911.2 95.0 1,840.0 0.0 0 0.00 0.000 05/12/09 1,181,402.9 94.1 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 0.1 0.2 05/15/09 7,732,742.6 106.0 1,840.0 0.0 0 0.00 0.000 0.2 05/15/09 1,239,884.3 106.8 1,840.0 0.0 0 0.00 0.000 0.1 05/15/09 1,334,108.9 109.4 1,840.0 0.0 0 0.00 0.000 0.1 05/14/09 1,366,426.7 112.3 1,840.0 0.0 0 0.00 0.000 0.1 05/14/09 1,349,620.2 114.9 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,228,126.7 116.3 1,840.0 0.0 0 0.00 0.000 0.1 05/14/09 1,159,265.6 116.6 1,840.0 0.0 0 0.00 0.000 0.1 05/14/09 1,168,336.6 116.4 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,312,474.5 116.3 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,144,186.7 114.2 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,247,877.1 112.9 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,234,519.6 111.1 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,199,724.6 107.6 1,840.0 0.0 0 0.00 0.000 0.1 05/14/09 935,211.9 104.0 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,453,387.6 112.7 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,305,580.9 110.6 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,289,352.0 109.1 1,840.0 0.0 0 0.00 0.000 0.1 05/14/09 1,332,710.9 107.4 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,317,739.0 105.51,840.0 0.0 0 0.00 0.000 0.1 05/14/09 1,346,304.3 102.3 1,840.0 0.0 0 0.00 0.000 0.2 05/14/09 1,259,422.8 98.8 1,840.0 0.0 0 0.00 0.000 2.4 05/14/09 1,325,860.8 97.6 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,282,383.1 97.6 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,281,630.6 98.7 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 7,660,785.8 100.1 1,840.0 0.0 0 0.00 0.000 0.0 05/14/09 1,290,473.1 101.7 1,840.0 0.0 0 0.00 0.000 0.1 05/14/09 1,314,758.0 102.3 1,840.0 0.0 0 0.00 0.000 0.0 05/13/09 1,256,995.3 103.9 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,338,426.6 105.4 1,840.0 0.0 0 0.00 0.000 0.2 05/13/09 1,468,970.2 107.9 1,840.0 0.0 0 0.00 0.000 0.3 05/13/09 1,431,829.0 106.9 1,840.0 0.0 0 0.00 0.000 0.2 05/13/09 1,449,573.8 108.4 1,840.0 0.0 0 0.00 0.000 0.2 05/13/09 1,259,135.1 106.9 1,840.0 0.0 0 0.00 0.000 0.2 05/13/09 1,315,723.0 105.7 1,840.0 0.0 0 0.00 0.000 0.1 05/13/09 1,444,660.0 103.6 1,840.0 0.0 0 0.00 0.000 0.0 05/13/09 1,368,474.1 100.8 1,840.0 0.0 0 0.00 0.000 05/13/09 1,515,653.0 98.0 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F FC 14:00 F F F F F F F F FC 15:00 F F F F F F F F FC 16:00 F F F F F F F F FC 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 0.1 0.1 05/16/09 1,441,398.7 98.8 1,840.0 0.0 0 0.00 0.000 0.1 05/16/09 1,528,437.2 100.3 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,571,886.3 102.51,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,434,742.8 103.4 1,840.0 0.0 0 0.00 0.000 0.1 05/16/09 1,379,219.5 105.51,840.0 0.0 0 0.00 0.000 0.1 05/16/09 1,482,514.3 104.4 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,416,002.0 102.51,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,481,476.6 100.6 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,508,437.4 98.8 1,840.0 0.0 0 0.00 0.000 0.1 05/16/09 1,647,704.1 100.2 1,840.0 0.0 0 0.00 0.000 2.3 05/16/09 1,342,282.5 99.8 1,840.0 0.0 0 0.00 0.000 0.1 05/16/09 1,391,684.9 101.3 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,278,491.9 101.51,840.0 0.0 0 0.00 0.000 0.0 05/16/09 7,772,517.3 102.7 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,328,415.3 102.6 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,405,765.0 103.0 1,840.0 0.0 0 0.00 0.000 0.1 05/15/09 1,467,489.3 105.2 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,482,946.8 107.0 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,410,352.5 107.9 1,840.0 0.0 0 0.00 0.000 0.1 05/15/09 1,413,951.7 109.51,840.0 0.0 0 0.00 0.000 0.1 05/15/09 1,466,663.7 109.0 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,369,217.4 108.8 1,840.0 0.0 0 0.00 0.000 1.9 05/15/09 1,454,258.4 108.7 1,840.0 0.0 0 0.00 0.000 3.1 05/15/09 1,362,262.7 108.6 1,840.0 0.0 0 0.00 0.000 4.6 05/15/09 1,430,480.3 108.51,840.0 0.0 0 0.00 0.000 0.1 05/15/09 1,372,276.9 107.4 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,386,617.4 106.51,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,305,463.6 104.6 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,329,489.4 102.3 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,354,605.6 100.0 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,277,194.1 98.8 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,282,822.7 99.3 1,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,331,918.6 100.0 1,840.0 0.0 0 0.00 0.000 0.1 05/15/09 1,348,359.5 101.2 1,840.0 0.0 0 0.00 0.000 2.4 05/15/09 1,267,494.9 102.51,840.0 0.0 0 0.00 0.000 0.0 05/15/09 1,315,799.2 103.4 1,840.0 0.0 0 0.00 0.000 05/15/09 1,215,881.3 104.3 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 2.4 0.0 05/18/09 1,311,093.7 98.2 1,840.0 0.0 0 0.00 0.000 0.1 05/18/09 1,294,850.6 98.9 1,840.0 0.0 0 0.00 0.000 0.1 05/18/09 7,787,135.8 100.8 1,840.0 0.0 0 0.00 0.000 0.1 05/18/09 1,452,919.1 102.6 1,840.0 0.0 0 0.00 0.000 0.1 05/18/09 1,468,738.6 104.4 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,442,931.5 107.0 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,335,717.1 107.9 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,243,908.8 107.2 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,325,556.9 106.51,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,277,705.2 105.6 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,230,469.4 104.1 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,267,407.1 102.6 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,201,686.4 99.2 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,247,045.8 98.2 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,287,174.1 99.1 1,840.0 0.0 0 0.00 0.000 0.2 05/17/09 1,255,931.8 98.51,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,267,602.8 99.0 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,192,546.6 98.4 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,238,280.8 98.0 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,278,584.0 97.2 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,229,307.1 96.3 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,270,704.5 95.51,840.0 0.0 0 0.00 0.000 0.2 05/17/09 1,337,024.6 94.51,840.0 0.0 0 0.00 0.000 2.4 05/17/09 1,333,077.2 95.1 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,247,306.5 95.2 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,244,082.6 95.6 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 7,629,753.5 95.9 1,840.0 0.0 0 0.00 0.000 0.0 05/17/09 1,190,615.7 96.2 1,840.0 0.0 0 0.00 0.000 0.1 05/17/09 1,145,713.8 96.6 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,252,981.8 97.51,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,325,081.2 97.3 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,274,083.8 97.7 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,256,137.7 97.51,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,297,883.7 97.3 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,305,449.7 97.0 1,840.0 0.0 0 0.00 0.000 0.0 05/16/09 1,448,239.9 97.6 1,840.0 0.0 0 0.00 0.000 05/16/09 1,487,496.3 98.4 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F FM 08:00 F F F F F F F F FM 09:00 F F F F F F F F FM 10:00 F F F F F F F F F 11:00 F F F F F F F F FC 12:00 F F F F F F F F FC 13:00 F F F F F F F F FC 14:00 F F F F F F F F FC 15:00 F F F F F F F F FC 16:00 F F F F F F F F FC 17:00 F F F F F F F F FC 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F FC 12:00 F F F F F F F F FC 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 0.0 0.0 05/19/09 1,319,695.0 114.8 1,840.0 0.0 0 0.00 0.000 0.1 05/19/09 1,313,824.2 114.51,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,356,982.2 115.0 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,329,474.3 114.6 1,840.0 0.0 0 0.00 0.000 1.4 05/19/09 1,384,893.8 115.3 1,840.0 0.0 0 0.00 0.000 2.2 05/19/09 1,407,407.4 115.1 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,253,842.9 113.8 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,202,467.7 112.9 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,206,705.5 111.4 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,244,018.7 109.3 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,280,380.0 107.0 1,840.0 0.0 0 0.00 0.000 0.1 05/19/09 1,225,506.1 104.2 1,840.0 0.0 0 0.00 0.000 2.4 05/19/09 1,358,949.6 100.51,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,369,022.7 101.0 1,840.0 0.0 0 0.00 0.000 1.9 05/19/09 1,421,806.8 101.8 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 7,858,957.2 104.1 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,539,825.5 104.6 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,525,205.5 106.7 1,840.0 0.0 0 0.00 0.000 0.1 05/18/09 1,488,266.7 108.9 1,840.0 0.0 0 0.00 0.000 0.0 05/18/09 1,492,498.1 112.0 1,840.0 0.0 0 0.00 0.000 0.0 05/18/09 1,359,994.3 113.1 1,840.0 0.0 0 0.00 0.000 0.0 05/18/09 1,366,061.0 112.9 1,840.0 0.0 0 0.00 0.000 0.0 05/18/09 1,256,205.9 112.2 1,840.0 0.0 0 0.00 0.000 2.4 05/18/09 1,269,350.4 111.2 1,840.0 0.0 0 0.00 0.000 4.3 05/18/09 1,313,778.4 110.4 1,840.0 0.0 0 0.00 0.000 0.0 05/18/09 1,342,377.6 109.4 1,840.0 0.0 0 0.00 0.000 2.9 05/18/09 1,422,245.5 108.8 1,840.0 0.0 0 0.00 0.000 2.0 05/18/09 1,458,475.9 109.3 1,840.0 0.0 0 0.00 0.000 2.1 05/18/09 1,583,560.6 110.7 1,840.0 0.0 0 0.00 0.000 0.8 05/18/09 1,446,571.4 111.3 1,840.0 0.0 0 0.00 0.000 3.4 05/18/09 1,403,068.2 111.6 1,840.0 0.0 0 0.00 0.000 0.0 05/18/09 1,382,000.0 110.51,840.0 0.0 0 0.00 0.000 0.2 05/18/09 1,292,418.3 108.9 1,840.0 0.0 0 0.00 0.000 0.2 05/18/09 1,310,709.5 106.7 1,840.0 9.3 0 0.00 1.766 0.000 0.1 05/18/09 1,331,677.8 103.3 1,840.0 0.0 0 0.00 0.000 0.1 05/18/09 1,375,244.1 101.0 1,840.0 0.0 0 0.00 0.000 05/18/09 1,326,956.6 97.6 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F FC 16:00 F F F F F F F F FC 17:00 F F F F F F F F FC 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 0.0 0.1 05/21/09 947,825.6 108.8 1,840.0 0.0 0 0.00 0.000 2.4 05/21/09 859,273.6 108.1 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 894,418.7 108.51,840.0 0.0 0 0.00 0.000 0.0 05/21/09 958,959.4 110.0 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 7,399,721.0 110.6 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 954,694.0 113.3 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 887,958.9 115.4 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 880,390.2 117.6 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 727,671.3 117.1 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 861,431.9 117.1 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 879,808.7 118.1 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 769,163.8 118.3 1,840.0 0.0 0 0.00 0.000 1.0 05/20/09 726,381.7 118.2 1,840.0 0.0 0 0.00 0.000 1.4 05/20/09 808,712.9 118.1 1,840.0 0.0 0 0.00 0.000 2.3 05/20/09 796,306.0 118.2 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 745,482.7 118.3 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 988,701.4 118.3 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,214,589.8 118.51,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,123,664.2 118.0 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,210,651.6 117.0 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,261,228.2 115.8 1,840.0 0.0 0 0.00 0.000 3.0 05/20/09 1,228,762.3 114.2 1,840.0 0.0 0 0.00 0.000 0.6 05/20/09 1,201,524.5 112.3 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,221,846.3 109.3 1,840.0 0.0 0 0.00 0.000 0.2 05/20/09 1,214,626.3 105.2 1,840.0 0.0 0 0.00 0.000 2.4 05/20/09 1,191,009.6 104.2 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,253,884.9 104.2 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,196,583.4 104.0 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 7,649,326.6 104.1 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,343,549.8 104.7 1,840.0 0.0 0 0.00 0.000 0.0 05/20/09 1,385,578.9 105.9 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,424,799.1 107.51,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,427,649.0 108.3 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,465,954.6 111.1 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,392,456.0 113.0 1,840.0 0.0 0 0.00 0.000 0.0 05/19/09 1,382,370.7 114.0 1,840.0 0.0 0 0.00 0.000 05/19/09 1,361,893.0 114.9 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 0.0 0.0 05/22/09 810,033.8 105.7 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 861,101.0 104.8 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 889,642.3 103.7 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 940,054.1 101.8 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 850,093.7 101.4 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,011,290.3 100.8 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,486,945.0 97.9 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,564,195.8 98.8 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,609,671.2 98.0 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,594,995.3 97.3 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,564,519.2 95.51,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,689,887.4 94.6 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 1,783,638.9 95.6 1,840.0 0.0 0 0.00 0.000 0.1 05/22/09 1,560,572.5 101.51,840.0 0.0 0 0.00 0.000 2.4 05/22/09 817,362.4 105.1 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 828,382.9 105.9 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 924,346.6 107.3 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 7,460,964.6 108.9 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 932,933.7 111.9 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 930,473.9 114.8 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 714,149.1 115.51,840.0 0.0 0 0.00 0.000 0.0 05/21/09 670,458.7 116.1 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 594,801.8 115.8 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 640,522.0 115.7 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 702,131.5 115.6 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 725,017.4 116.2 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 748,625.7 117.6 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 856,026.0 120.9 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 653,162.0 122.9 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 546,008.2 121.8 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 563,559.3 120.7 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 683,498.6 118.8 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 644,452.9 116.3 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 506,722.9 115.9 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 855,745.6 112.0 1,840.0 0.0 0 0.00 0.000 0.0 05/21/09 805,030.5 109.2 1,840.0 0.0 0 0.00 0.000 05/21/09 891,885.4 108.4 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 0.0 0.0 05/24/09 990,815.3 106.4 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 921,352.6 105.8 1,840.0 0.0 0 0.00 0.000 0.1 05/24/09 974,720.6 106.3 1,840.0 0.0 0 0.00 0.000 2.4 05/24/09 931,693.0 106.2 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 924,026.0 107.3 1,840.0 0.0 0 0.00 0.000 0.1 05/24/09 983,944.6 108.2 1,840.0 0.0 0 0.00 0.000 0.1 05/24/09 7,481,790.4 108.51,840.0 0.0 0 0.00 0.000 0.0 05/24/09 1,115,396.6 112.9 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 1,026,949.4 112.9 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 946,696.8 114.51,840.0 0.0 0 0.00 0.000 0.0 05/23/09 869,925.5 114.9 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 900,127.2 114.7 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 857,476.5 114.3 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 881,105.9 113.51,840.0 0.0 0 0.00 0.000 0.0 05/23/09 879,667.9 113.0 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 913,014.6 112.0 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 877,823.4 110.8 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 913,333.4 109.8 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 826,010.4 108.51,840.0 0.0 0 0.00 0.000 0.0 05/23/09 855,489.9 107.0 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 830,151.2 105.4 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 831,509.7 103.6 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 924,451.3 100.4 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 896,196.9 99.3 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 964,251.8 99.8 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 956,309.8 99.8 1,840.0 0.0 0 0.00 0.000 0.1 05/23/09 961,520.1 100.3 1,840.0 0.0 0 0.00 0.000 2.4 05/23/09 990,809.8 101.1 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 981,423.1 102.2 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 1,010,996.4 103.51,840.0 0.0 0 0.00 0.000 0.0 05/23/09 7,492,516.9 105.1 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 1,048,970.9 107.1 1,840.0 0.0 0 0.00 0.000 0.0 05/23/09 997,808.4 108.0 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 882,690.4 108.6 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 896,554.1 108.0 1,840.0 0.0 0 0.00 0.000 0.0 05/22/09 834,177.7 106.9 1,840.0 0.0 0 0.00 0.000 05/22/09 854,648.7 106.3 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 11:00 12:00 13:00 C 14:00 C 15:00 16:00 C ST ST 17:00 ST ST 18:00 ST ST 19:00 ST ST 20:00 ST ST 21:00 ST ST 0.0 0.0 05/25/09 23,290,819.2 214.3 1,840.0 493.7 0 60.00 0.000 0.000 0.1 05/25/09 23,489,516.9 212.51,840.0 497.9 0 60.00 0.000 0.000 0.1 05/25/09 23,425,448.6 207.8 1,840.0 496.5 0 60.00 0.294 0.002 0.1 05/25/09 22,530,452.9 200.9 1,840.0 477.5 0 60.00 0.294 0.002 0.7 05/25/09 21,786,183.6 190.51,840.0 461.8 0 60.00 0.294 0.002 0.4 05/25/09 21,102,263.5 162.51,840.0 447.3 0 60.00 2.061 0.015 0.3 05/25/09 21,015,767.4 143.0 1,840.0 148.5 0 60.00 3.533 0.008 0.2 05/25/09 21,090,352.6 128.7 1,840.0 114.6 0 60.00 3.444 0.006 0.2 05/25/09 21,429,401.9 111.4 1,840.0 116.5 0 60.00 2.296 0.004 0.1 05/25/09 21,587,417.1 93.1 1,840.0 117.3 0 60.00 2.296 0.004 0.0 05/25/09 21,409,237.4 82.4 1,840.0 81.4 0 53.00 1.640 0.002 0.0 05/25/09 20,456,464.0 79.7 1,840.0 1.0 0 4.00 0.000 0.0 05/25/09 1,079,277.6 95.1 1,840.0 0.0 0 0.00 0.000 0.0 05/25/09 1,035,531.4 94.9 1,840.0 0.0 0 0.00 0.000 0.0 05/25/09 1,048,067.3 95.0 1,840.0 0.0 0 0.00 0.000 0.1 05/25/09 1,094,086.5 94.8 1,840.0 0.0 0 0.00 0.000 2.3 05/25/09 1,169,396.5 95.4 1,840.0 0.0 0 0.00 0.000 0.0 05/25/09 1,093,156.2 97.1 1,840.0 0.0 0 0.00 0.000 0.0 05/25/09 1,070,790.1 97.0 1,840.0 0.0 0 0.00 0.000 0.0 05/25/09 7,467,938.3 97.7 1,840.0 0.0 0 0.00 0.000 0.1 05/25/09 1,171,707.1 100.4 1,840.0 0.0 0 0.00 0.000 0.1 05/25/09 1,088,689.2 103.3 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 1,051,386.4 106.4 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 921,265.1 106.3 1,840.0 0.0 0 0.00 0.000 0.1 05/24/09 916,290.0 107.1 1,840.0 0.0 0 0.00 0.000 0.1 05/24/09 904,324.0 105.9 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 885,890.4 105.2 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 906,657.6 104.2 1,840.0 0.0 0 0.00 0.000 0.1 05/24/09 961,276.2 103.0 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 1,004,096.6 103.2 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 943,957.4 102.3 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 919,426.4 102.7 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 890,106.9 102.9 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 969,157.9 104.3 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 1,024,145.3 104.6 1,840.0 0.0 0 0.00 0.000 0.0 05/24/09 998,389.5 105.8 1,840.0 0.0 0 0.00 0.000 05/24/09 963,214.0 106.2 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 ST ST 23:00 ST ST 00:00 ST ST 01:00 ST ST 02:00 C ST ST 03:00 ST ST 04:00 ST ST C 05:00 C ST ST C 06:00 ST ST 07:00 ST ST 08:00 09:00 10:00 11:00 C 12:00 C 13:00 M M C 14:00 C 15:00 C 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 3.7 4.0 05/27/09 40,262,853.5 285.4 1,840.02,997.8 271 60.00 3.101 0.149 4.1 05/27/09 40,002,888.2 282.7 1,840.02,913.3 266 60.00 3.427 0.160 4.4 05/27/09 37,527,503.8 282.2 1,840.02,773.8 250 60.00 3.461 0.154 4.7 05/27/09 38,408,994.1 282.8 1,840.02,797.2 251 60.00 3.770 0.169 4.7 05/27/09 37,425,022.9 281.1 1,840.02,664.5 237 60.00 4.119 0.176 4.0 05/27/09 35,372,796.9 275.9 1,840.02,576.1 226 60.00 4.027 0.166 4.0 05/27/09 29,172,864.3 270.6 1,840.02,061.1 185 60.00 3.533 0.116 3.6 05/27/09 28,767,404.3 267.51,840.02,063.7 182 60.00 3.479 0.115 3.7 05/27/09 25,368,162.5 265.9 1,840.0 1,682.0 159 60.00 3.388 0.091 3.7 05/27/09 25,761,817.0 265.6 1,840.0 1,722.1 156 60.00 3.454 0.095 3.8 05/27/09 25,354,177.2 266.3 1,840.0 1,694.9 153 60.00 3.454 0.094 4.4 05/26/09 25,763,252.5 273.3 1,840.0 1,750.2 168 60.00 3.490 0.098 4.4 05/26/09 34,591,997.8 276.7 1,840.02,538.0 228 60.00 3.742 0.152 4.5 05/26/09 34,229,796.1 274.9 1,840.02,511.4 225 60.00 3.742 0.150 4.2 05/26/09 35,837,153.0 269.9 1,840.02,590.4 237 60.00 3.885 0.161 4.0 05/26/09 36,642,432.5 262.4 1,840.02,648.6 242 60.00 3.626 0.154 3.8 05/26/09 36,063,320.8 257.51,840.02,626.3 238 60.00 3.427 0.144 3.8 05/26/09 34,545,908.2 257.1 1,840.02,572.2 232 60.00 3.185 0.131 4.0 05/26/09 33,757,754.3 258.1 1,840.02,458.5 223 60.00 3.256 0.128 4.2 05/26/09 33,772,000.4 258.3 1,840.02,459.5 223 60.00 3.427 0.135 4.2 05/26/09 33,700,083.8 255.3 1,840.02,435.9 221 60.00 3.626 0.141 3.4 05/26/09 29,465,732.4 247.3 1,840.02,177.9 194 60.00 3.546 0.123 3.4 05/26/09 26,992,897.8 242.6 1,840.0 1,775.1 150 60.00 3.226 0.092 3.4 05/26/09 25,863,353.5 245.51,840.0 1,714.8 149 60.00 3.200 0.088 2.5 05/26/09 29,785,498.9 244.0 1,840.0 1,732.1 139 60.00 3.648 0.101 1.6 05/26/09 25,658,387.5 235.0 1,840.0 1,199.2 90 60.00 3.338 0.064 1.5 05/26/09 23,588,766.6 228.1 1,840.0 833.3 48 60.00 2.826 0.038 1.0 05/26/09 23,248,502.1 222.1 1,840.0 492.8 36 60.00 4.416 0.035 1.0 05/26/09 20,791,356.3 218.7 1,840.0 440.7 18 60.00 2.944 0.021 0.5 05/26/09 21,932,464.0 219.4 1,840.0 464.9 16 60.00 2.944 0.022 0.4 05/26/09 24,588,723.1 218.6 1,840.0 521.2 9 60.00 1.472 0.012 0.2 05/26/09 24,049,559.7 215.9 1,840.0 509.8 0 60.00 1.178 0.010 0.1 05/26/09 23,868,713.4 215.6 1,840.0 505.9 0 60.00 0.589 0.005 0.0 05/26/09 23,367,241.7 214.7 1,840.0 495.3 0 60.00 0.294 0.002 0.0 05/26/09 23,406,526.5 214.8 1,840.0 496.1 0 60.00 0.000 0.000 0.1 05/25/09 23,554,592.0 215.4 1,840.0 499.3 0 60.00 0.000 0.000 05/25/09 23,331,377.5 214.4 1,840.0 494.5 0 60.00 0.294 0.002

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 2.6 2.6 05/28/09 24,800,577.8 268.7 1,840.0 1,765.7 155 60.00 2.279 0.064 3.2 05/28/09 25,506,265.2 270.0 1,840.0 1,843.6 159 60.00 2.245 0.066 4.1 05/28/09 26,987,030.8 276.0 1,840.0 1,936.0 176 60.00 2.783 0.086 4.4 05/28/09 36,745,575.8 283.1 1,840.02,656.1 243 60.00 3.539 0.150 4.0 05/28/09 36,758,921.3 279.0 1,840.02,657.0 239 60.00 3.798 0.161 4.1 05/28/09 32,787,950.0 275.3 1,840.02,352.2 211 60.00 3.479 0.131 3.3 05/28/09 32,922,683.4 276.3 1,840.02,415.5 217 60.00 3.487 0.135 3.7 05/28/09 33,664,261.3 278.7 1,840.02,469.9 223 60.00 2.807 0.111 3.9 05/28/09 36,575,870.1 281.9 1,840.02,723.3 244 60.00 3.101 0.135 4.6 05/28/09 37,355,512.9 283.2 1,840.02,781.4 250 60.00 3.268 0.145 4.7 05/28/09 39,950,042.9 288.1 1,840.02,996.3 272 60.00 3.827 0.183 4.5 05/28/09 40,753,458.6 287.8 1,840.03,078.6 281 60.00 3.882 0.191 3.7 05/28/09 40,437,154.6 285.0 1,840.03,054.8 276 60.00 3.717 0.182 3.7 05/28/09 37,321,729.1 280.4 1,840.02,819.4 251 60.00 3.056 0.138 3.9 05/28/09 36,341,040.0 282.51,840.02,705.8 242 60.00 3.101 0.134 3.3 05/28/09 39,985,412.0 284.8 1,840.02,998.9 273 60.00 3.245 0.156 3.2 05/28/09 39,850,234.0 283.6 1,840.02,967.1 272 60.00 2.766 0.131 2.2 05/28/09 37,552,443.1 276.7 1,840.02,796.0 248 60.00 2.682 0.120 2.2 05/28/09 30,286,657.5 272.4 1,840.02,189.2 191 60.00 1.899 0.066 1.7 05/28/09 29,777,199.0 272.9 1,840.02,136.2 187 60.00 1.914 0.065 2.3 05/28/09 27,601,078.0 269.6 1,840.0 1,980.1 171 60.00 1.479 0.047 2.2 05/28/09 24,414,833.7 268.4 1,840.0 1,725.0 152 60.00 2.031 0.056 2.3 05/28/09 25,021,499.0 269.4 1,840.0 1,795.0 157 60.00 1.914 0.055 2.9 05/28/09 25,309,257.8 269.8 1,840.0 1,815.6 160 60.00 2.001 0.058 3.6 05/27/09 26,337,341.1 274.4 1,840.0 1,889.4 173 60.00 2.522 0.076 4.2 05/27/09 33,554,347.2 280.51,840.02,443.6 224 60.00 3.085 0.121 4.2 05/27/09 39,437,995.1 285.3 1,840.02,893.5 266 60.00 3.572 0.165 4.0 05/27/09 41,527,829.1 286.7 1,840.03,046.9 282 60.00 3.572 0.174 4.0 05/27/09 41,395,371.2 286.6 1,840.03,037.1 280 60.00 3.402 0.165 3.9 05/27/09 40,533,249.8 285.51,840.02,973.9 273 60.00 3.402 0.162 3.9 05/27/09 40,282,479.8 287.2 1,840.03,043.0 280 60.00 3.221 0.157 3.9 05/27/09 41,361,814.0 288.3 1,840.03,192.1 293 60.00 3.153 0.161 3.9 05/27/09 41,777,111.8 288.9 1,840.03,224.1 296 60.00 3.153 0.163 3.2 05/27/09 41,601,809.9 287.1 1,840.03,233.2 297 60.00 3.131 0.162 3.2 05/27/09 41,486,619.7 286.9 1,840.03,179.2 296 60.00 2.606 0.132 3.3 05/27/09 39,788,151.4 286.8 1,840.03,092.2 282 60.00 2.569 0.127 05/27/09 40,039,504.8 285.7 1,840.03,003.0 272 60.00 2.746 0.132

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 2.8 2.9 05/30/09 29,687,516.0 277.8 1,840.02,129.8 197 60.00 2.435 0.083 2.7 05/30/09 36,718,534.0 278.0 1,840.02,793.8 244 60.00 2.378 0.106 1.9 05/30/09 35,487,363.6 278.0 1,840.02,603.7 234 60.00 2.296 0.096 2.0 05/30/09 33,286,697.6 274.7 1,840.02,460.3 216 60.00 1.604 0.063 2.0 05/30/09 29,882,669.8 273.3 1,840.02,143.8 190 60.00 1.740 0.060 2.2 05/30/09 32,625,886.4 273.1 1,840.02,340.6 206 60.00 1.740 0.065 2.5 05/30/09 26,745,843.2 269.6 1,840.0 1,831.5 166 60.00 2.005 0.059 1.7 05/30/09 28,462,450.5 269.6 1,840.02,072.8 180 60.00 2.142 0.071 1.8 05/30/09 25,530,679.3 269.8 1,840.0 1,831.6 157 60.00 1.479 0.043 1.8 05/30/09 25,552,572.3 270.7 1,840.0 1,819.3 156 60.00 1.578 0.046 2.8 05/30/09 26,360,876.0 269.51,840.0 1,848.1 162 60.00 1.602 0.047 2.6 05/30/09 24,999,054.6 268.2 1,840.0 1,752.6 152 60.00 2.492 0.070 2.5 05/30/09 24,815,845.9 268.3 1,840.0 1,766.8 152 60.00 2.279 0.064 2.3 05/29/09 24,909,705.2 268.1 1,840.0 1,787.0 153 60.00 2.175 0.062 2.2 05/29/09 24,478,266.9 268.6 1,840.0 1,769.3 153 60.00 1.986 0.056 2.5 05/29/09 25,960,390.2 272.2 1,840.0 1,890.6 168 60.00 1.885 0.057 2.3 05/29/09 29,207,859.7 273.2 1,840.02,143.0 189 60.00 2.126 0.073 2.9 05/29/09 27,716,571.9 273.6 1,840.02,003.5 177 60.00 1.986 0.064 3.7 05/29/09 30,927,506.0 279.0 1,840.02,269.2 205 60.00 2.466 0.089 4.2 05/29/09 35,499,906.7 281.8 1,840.02,643.2 238 60.00 3.101 0.131 4.2 05/29/09 40,936,328.8 285.4 1,840.03,025.7 276 60.00 3.546 0.172 4.1 05/29/09 41,347,409.2 286.7 1,840.03,033.6 276 60.00 3.572 0.173 4.2 05/29/09 42,131,694.3 287.2 1,840.03,137.0 283 60.00 3.436 0.172 4.6 05/29/09 41,930,719.3 286.8 1,840.03,076.5 279 60.00 3.572 0.176 4.4 05/29/09 42,095,658.0 286.1 1,840.03,042.8 280 60.00 3.971 0.193 4.3 05/29/09 41,972,505.2 285.2 1,840.02,988.3 281 60.00 3.856 0.184 3.9 05/29/09 42,284,102.8 287.0 1,840.02,941.5 282 60.00 3.857 0.181 3.8 05/29/09 41,592,574.5 285.51,840.03,096.9 276 60.00 3.268 0.162 3.7 05/29/09 40,695,883.4 285.6 1,840.03,074.3 272 60.00 3.139 0.154 3.6 05/29/09 40,541,187.2 286.8 1,840.03,084.6 272 60.00 3.034 0.150 2.8 05/29/09 37,819,564.9 279.1 1,840.02,836.5 246 60.00 2.995 0.136 2.8 05/29/09 30,188,616.6 269.8 1,840.02,215.0 190 60.00 2.381 0.084 2.6 05/29/09 24,803,760.1 267.7 1,840.0 1,739.0 154 60.00 2.492 0.069 2.6 05/29/09 25,440,215.0 267.8 1,840.0 1,838.9 158 60.00 2.245 0.066 2.6 05/29/09 25,044,510.5 268.1 1,840.0 1,769.5 152 60.00 2.296 0.065 2.6 05/29/09 25,098,823.6 268.2 1,840.0 1,773.3 151 60.00 2.296 0.065 05/29/09 25,265,513.6 267.6 1,840.0 1,785.1 153 60.00 2.296 0.066

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 1.4 1.4 06/01/09 24,595,906.9 268.4 1,840.0 1,791.2 151 60.00 1.200 0.034 1.7 06/01/09 24,740,712.4 268.51,840.0 1,761.5 151 60.00 1.227 0.035 1.9 05/31/09 25,015,931.8 268.6 1,840.0 1,821.8 157 60.00 1.457 0.042 1.9 05/31/09 24,707,354.7 267.51,840.0 1,812.7 156 60.00 1.616 0.047 2.7 05/31/09 24,266,723.7 271.4 1,840.0 1,754.1 155 60.00 1.640 0.046 2.7 05/31/09 32,428,190.3 279.7 1,840.02,326.4 214 60.00 2.349 0.087 2.4 05/31/09 36,095,099.8 276.4 1,840.02,530.6 227 60.00 2.403 0.097 2.6 05/31/09 31,840,915.4 275.1 1,840.02,249.6 202 60.00 2.120 0.076 2.4 05/31/09 32,510,378.1 276.1 1,840.02,367.6 214 60.00 2.228 0.084 1.9 05/31/09 34,403,896.0 277.8 1,840.02,524.2 228 60.00 2.041 0.082 1.4 05/31/09 35,061,407.8 274.7 1,840.02,667.7 234 60.00 1.558 0.066 1.4 05/31/09 28,481,657.3 271.2 1,840.02,151.6 188 60.00 1.156 0.040 1.3 05/31/09 28,248,462.8 272.2 1,840.02,087.9 185 60.00 1.182 0.039 1.9 05/31/09 27,637,358.5 270.7 1,840.02,057.8 179 60.00 1.089 0.036 1.7 05/31/09 27,619,938.0 271.8 1,840.02,056.5 185 60.00 1.592 0.052 1.8 05/31/09 29,488,831.9 272.51,840.02,259.8 200 60.00 1.384 0.050 1.5 05/31/09 29,477,502.5 270.1 1,840.02,226.9 194 60.00 1.487 0.053 1.2 05/31/09 27,731,993.1 267.6 1,840.02,034.7 178 60.00 1.276 0.042 1.6 05/31/09 25,625,711.7 268.2 1,840.0 1,880.2 161 60.00 1.021 0.031 1.3 05/31/09 26,868,471.0 271.0 1,840.0 1,927.5 172 60.00 1.392 0.043 1.3 05/31/09 28,206,889.0 267.7 1,840.02,054.2 174 60.00 1.114 0.037 1.4 05/31/09 23,964,430.7 266.7 1,840.0 1,732.2 151 60.00 1.122 0.031 1.4 05/31/09 25,005,029.0 267.7 1,840.0 1,793.8 157 60.00 1.218 0.035 1.6 05/31/09 24,841,889.6 267.9 1,840.0 1,741.6 153 60.00 1.246 0.035 1.6 05/31/09 25,167,452.9 267.2 1,840.0 1,805.5 154 60.00 1.392 0.040 1.7 05/31/09 24,572,144.1 266.6 1,840.0 1,762.8 153 60.00 1.392 0.039 1.5 05/30/09 24,419,914.4 266.2 1,840.0 1,765.1 153 60.00 1.468 0.041 1.6 05/30/09 24,227,415.6 267.7 1,840.0 1,777.5 154 60.00 1.276 0.036 2.0 05/30/09 26,693,763.7 274.4 1,840.0 1,915.0 177 60.00 1.392 0.043 2.0 05/30/09 35,212,533.9 276.9 1,840.02,621.8 235 60.00 1.676 0.070 1.9 05/30/09 33,483,672.4 276.6 1,840.02,456.7 223 60.00 1.701 0.067 1.7 05/30/09 35,802,676.3 276.2 1,840.02,665.8 239 60.00 1.592 0.068 1.5 05/30/09 34,480,290.9 276.7 1,840.02,567.3 229 60.00 1.425 0.058 1.9 05/30/09 29,951,559.6 270.4 1,840.02,181.3 187 60.00 1.285 0.045 1.6 05/30/09 26,782,370.1 269.51,840.0 1,935.9 171 60.00 1.640 0.051 1.8 05/30/09 26,346,154.3 267.9 1,840.0 1,918.7 166 60.00 1.371 0.042 05/30/09 23,739,025.0 269.8 1,840.0 1,754.6 152 60.00 1.520 0.043

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 1.5 2.3 06/02/09 33,748,159.1 277.6 1,840.02,512.8 222 60.00 1.257 0.051 2.4 06/02/09 38,997,056.8 282.4 1,840.02,946.0 265 60.00 1.900 0.089 2.3 06/02/09 40,694,864.6 283.1 1,840.03,074.2 277 60.00 1.982 0.097 2.2 06/02/09 40,866,064.2 283.3 1,840.03,087.2 276 60.00 1.900 0.094 2.3 06/02/09 39,706,768.7 282.1 1,840.02,978.0 265 60.00 1.830 0.087 2.0 06/02/09 40,340,878.2 281.9 1,840.03,025.6 273 60.00 1.914 0.093 2.0 06/02/09 40,885,310.3 281.7 1,840.03,044.2 274 60.00 1.676 0.082 1.6 06/02/09 39,487,725.4 279.51,840.02,897.2 257 60.00 1.701 0.079 1.7 06/02/09 34,130,056.8 273.1 1,840.02,541.2 218 60.00 1.341 0.054 1.5 06/02/09 27,869,751.6 266.6 1,840.0 1,999.4 169 60.00 1.479 0.047 1.3 06/02/09 25,076,125.3 267.2 1,840.0 1,785.3 152 60.00 1.315 0.038 1.5 06/02/09 25,568,302.0 267.51,840.0 1,820.3 154 60.00 1.139 0.033 1.5 06/02/09 25,232,344.0 267.3 1,840.0 1,796.4 151 60.00 1.315 0.038 1.5 06/02/09 24,645,638.6 266.6 1,840.0 1,781.5 151 60.00 1.295 0.037 1.8 06/02/09 24,452,486.1 266.51,840.0 1,780.7 151 60.00 1.285 0.037 1.8 06/01/09 24,668,125.4 266.4 1,840.0 1,809.9 153 60.00 1.531 0.044 1.4 06/01/09 24,522,920.3 266.7 1,840.0 1,799.2 152 60.00 1.531 0.044 1.4 06/01/09 25,841,778.8 270.9 1,840.0 1,910.1 167 60.00 1.182 0.036 1.3 06/01/09 31,931,066.3 274.2 1,840.02,412.2 212 60.00 1.156 0.045 1.6 06/01/09 28,651,564.0 269.8 1,840.02,133.3 178 60.00 1.089 0.037 2.7 06/01/09 28,075,269.3 277.2 1,840.02,090.4 187 60.00 1.341 0.045 2.4 06/01/09 39,611,083.9 282.4 1,840.02,992.4 272 60.00 2.230 0.107 2.4 06/01/09 41,429,926.3 282.8 1,840.03,039.7 277 60.00 2.041 0.099 2.5 06/01/09 40,919,774.8 282.9 1,840.03,046.8 277 60.00 2.011 0.098 2.4 06/01/09 41,088,399.6 283.1 1,840.03,059.3 277 60.00 2.095 0.102 2.1 06/01/09 41,638,371.8 284.0 1,840.03,077.6 277 60.00 2.026 0.100 2.0 06/01/09 40,880,279.9 282.9 1,840.03,043.8 273 60.00 1.760 0.086 1.9 06/01/09 39,202,423.0 282.0 1,840.02,961.5 264 60.00 1.652 0.078 1.8 06/01/09 38,019,674.8 278.6 1,840.02,789.5 248 60.00 1.616 0.072 1.8 06/01/09 35,186,449.9 276.0 1,840.02,562.5 227 60.00 1.542 0.063 1.6 06/01/09 35,948,425.5 277.1 1,840.02,539.8 229 60.00 1.590 0.065 1.3 06/01/09 36,123,625.0 274.3 1,840.02,591.5 225 60.00 1.392 0.058 1.7 06/01/09 28,597,729.9 270.4 1,840.02,051.6 177 60.00 1.131 0.037 1.6 06/01/09 26,781,855.1 268.51,840.0 1,979.5 171 60.00 1.435 0.045 1.8 06/01/09 24,189,290.6 267.8 1,840.0 1,801.0 154 60.00 1.341 0.039 1.3 06/01/09 24,930,187.3 267.51,840.0 1,842.7 158 60.00 1.520 0.045 06/01/09 24,461,427.5 268.4 1,840.0 1,808.0 153 60.00 1.098 0.032

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 1.6 1.7 06/04/09 26,966,352.9 262.7 1,840.0 1,802.6 165 60.00 1.494 0.043 2.1 06/04/09 25,287,795.0 262.8 1,840.0 1,676.7 154 60.00 1.600 0.043 2.1 06/04/09 24,550,526.1 262.9 1,840.0 1,641.2 151 60.00 1.960 0.051 2.4 06/04/09 24,972,230.6 263.9 1,840.0 1,655.8 152 60.00 1.976 0.052 2.6 06/03/09 26,244,001.1 263.7 1,840.0 1,782.9 162 60.00 2.204 0.063 2.5 06/03/09 25,089,302.1 263.1 1,840.0 1,731.7 152 60.00 2.351 0.065 2.5 06/03/09 24,679,778.5 267.8 1,840.0 1,703.5 156 60.00 2.260 0.062 2.1 06/03/09 34,186,490.9 273.4 1,840.02,452.5 229 60.00 2.175 0.085 2.1 06/03/09 32,013,178.7 266.8 1,840.02,227.0 202 60.00 1.884 0.067 2.1 06/03/09 27,979,829.3 264.51,840.0 1,916.0 175 60.00 1.914 0.059 2.1 06/03/09 26,793,006.9 266.51,840.0 1,849.3 171 60.00 1.899 0.056 2.5 06/03/09 30,371,314.0 271.2 1,840.02,129.3 200 60.00 1.869 0.064 2.7 06/03/09 35,289,185.0 275.2 1,840.02,531.6 236 60.00 2.175 0.088 3.2 06/03/09 38,350,857.4 275.0 1,840.02,793.0 258 60.00 2.313 0.103 3.5 06/03/09 39,485,727.9 276.8 1,840.02,725.4 260 60.00 2.893 0.126 3.4 06/03/09 41,091,414.0 277.8 1,840.02,836.2 273 60.00 3.164 0.144 3.6 06/03/09 41,528,041.5 278.2 1,840.02,866.3 274 60.00 3.074 0.141 3.5 06/03/09 40,964,915.8 277.1 1,840.02,916.5 272 60.00 3.155 0.147 3.1 06/03/09 41,071,312.7 277.0 1,840.03,035.7 273 60.00 2.955 0.143 2.4 06/03/09 41,206,408.1 277.4 1,840.03,068.1 272 60.00 2.598 0.127 1.9 06/03/09 41,185,489.6 276.6 1,840.03,066.5 271 60.00 2.011 0.099 1.3 06/03/09 37,113,226.5 270.9 1,840.02,803.6 240 60.00 1.569 0.070 1.8 06/03/09 30,167,898.8 264.51,840.02,246.2 186 60.00 1.089 0.039 1.5 06/03/09 24,812,037.3 262.8 1,840.0 1,833.9 153 60.00 1.520 0.045 1.6 06/03/09 25,395,456.5 262.7 1,840.0 1,794.2 154 60.00 1.325 0.038 1.4 06/03/09 25,542,791.0 262.4 1,840.0 1,832.4 151 60.00 1.392 0.041 1.3 06/03/09 25,148,675.1 263.1 1,840.0 1,817.8 151 60.00 1.209 0.035 1.2 06/03/09 25,165,680.4 264.1 1,840.0 1,819.1 151 60.00 1.122 0.033 1.7 06/02/09 25,370,571.6 266.1 1,840.0 1,875.2 154 60.00 1.013 0.030 1.8 06/02/09 26,576,964.9 269.1 1,840.0 1,978.8 153 60.00 1.425 0.045 1.2 06/02/09 32,608,185.9 274.8 1,840.02,445.6 205 60.00 1.498 0.059 0.9 06/02/09 31,294,715.3 271.7 1,840.02,432.2 200 60.00 0.963 0.037 0.7 06/02/09 27,739,202.0 269.6 1,840.02,080.4 172 60.00 0.749 0.025 1.4 06/02/09 25,749,475.2 269.0 1,840.0 1,917.2 156 60.00 0.587 0.018 1.3 06/02/09 25,779,718.2 271.7 1,840.0 1,905.5 164 60.00 1.182 0.036 1.4 06/02/09 31,408,781.6 275.6 1,840.02,338.6 208 60.00 1.089 0.041 06/02/09 35,014,704.3 276.1 1,840.02,645.2 230 60.00 1.156 0.049

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 0.7 0.5 06/05/09 34,110,788.6 275.0 1,840.02,447.1 228 60.00 0.609 0.024 0.8 06/05/09 38,954,026.8 277.6 1,840.02,815.7 264 60.00 0.432 0.019 1.6 06/05/09 38,252,506.1 277.6 1,840.02,744.2 258 60.00 0.696 0.031 1.9 06/05/09 39,038,484.4 278.4 1,840.02,779.3 262 60.00 1.402 0.062 1.8 06/05/09 39,565,101.7 277.1 1,840.02,773.9 265 60.00 1.691 0.075 1.4 06/05/09 37,694,305.3 274.7 1,840.02,724.6 253 60.00 1.554 0.068 1.4 06/05/09 35,030,515.3 273.6 1,840.02,513.1 230 60.00 1.218 0.049 1.5 06/05/09 36,085,042.8 274.3 1,840.02,569.1 239 60.00 1.227 0.050 1.7 06/05/09 35,705,333.5 274.3 1,840.02,542.0 234 60.00 1.315 0.053 1.7 06/05/09 36,472,408.3 274.51,840.02,636.3 248 60.00 1.468 0.062 1.4 06/05/09 35,523,242.5 270.2 1,840.02,567.7 234 60.00 1.468 0.060 1.5 06/05/09 28,909,597.2 263.8 1,840.0 1,979.7 176 60.00 1.276 0.040 1.3 06/05/09 25,197,825.1 263.3 1,840.0 1,670.7 152 60.00 1.412 0.038 1.4 06/05/09 25,379,264.2 262.6 1,840.0 1,710.3 154 60.00 1.204 0.033 1.4 06/05/09 24,154,639.4 262.6 1,840.0 1,641.0 151 60.00 1.286 0.034 1.5 06/05/09 23,989,009.1 264.3 1,840.0 1,629.7 150 60.00 1.286 0.034 1.3 06/05/09 25,330,885.2 264.3 1,840.0 1,762.2 151 60.00 1.345 0.038 1.4 06/04/09 25,523,891.9 263.4 1,840.0 1,734.0 152 60.00 1.194 0.033 1.4 06/04/09 24,695,668.0 264.2 1,840.0 1,691.1 152 60.00 1.276 0.034 1.9 06/04/09 26,428,171.2 269.51,840.0 1,824.1 169 60.00 1.266 0.037 1.8 06/04/09 35,272,538.5 276.7 1,840.02,492.1 235 60.00 1.678 0.067 1.8 06/04/09 37,209,128.1 272.8 1,840.02,669.3 240 60.00 1.566 0.067 1.8 06/04/09 30,975,443.2 268.8 1,840.02,188.5 197 60.00 1.590 0.056 1.7 06/04/09 29,304,129.7 270.0 1,840.02,086.3 187 60.00 1.578 0.053 1.6 06/04/09 34,051,532.1 273.8 1,840.02,442.9 228 60.00 1.479 0.058 1.9 06/04/09 37,756,779.4 277.0 1,840.02,770.2 258 60.00 1.361 0.060 2.0 06/04/09 39,124,607.6 278.0 1,840.02,891.8 270 60.00 1.604 0.074 2.3 06/04/09 38,064,893.1 277.2 1,840.02,730.8 255 60.00 1.740 0.076 2.3 06/04/09 38,782,347.5 277.2 1,840.02,803.3 264 60.00 1.986 0.089 2.1 06/04/09 39,157,118.3 277.3 1,840.02,851.7 266 60.00 1.971 0.090 2.5 06/04/09 39,815,419.6 278.3 1,840.02,899.6 272 60.00 1.799 0.083 2.6 06/04/09 40,139,737.8 278.1 1,840.02,901.4 273 60.00 2.158 0.100 2.5 06/04/09 40,707,722.9 277.51,840.02,920.4 274 60.00 2.262 0.106 2.2 06/04/09 39,910,662.2 275.2 1,840.02,884.9 271 60.00 2.158 0.100 1.6 06/04/09 36,924,953.7 270.0 1,840.02,649.0 243 60.00 1.914 0.081 2.0 06/04/09 29,415,768.6 264.0 1,840.02,046.3 182 60.00 1.435 0.047 06/04/09 25,264,603.2 264.3 1,840.0 1,702.6 155 60.00 1.852 0.050

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 2.3 2.5 06/07/09 24,756,262.7 262.6 1,840.0 1,722.2 152 60.00 2.063 0.057 2.3 06/07/09 25,372,928.0 262.3 1,840.0 1,709.9 152 60.00 2.315 0.063 2.2 06/07/09 25,425,455.1 261.9 1,840.0 1,699.6 151 60.00 2.147 0.058 2.2 06/07/09 24,872,278.6 262.3 1,840.0 1,689.7 151 60.00 2.021 0.055 2.3 06/07/09 25,018,219.7 262.51,840.0 1,726.8 152 60.00 1.989 0.055 2.2 06/07/09 25,504,924.7 262.6 1,840.0 1,746.5 153 60.00 2.096 0.059 2.2 06/06/09 25,302,880.6 263.2 1,840.0 1,760.2 155 60.00 1.973 0.056 2.5 06/06/09 24,881,465.0 265.3 1,840.0 1,690.3 152 60.00 2.021 0.055 2.6 06/06/09 29,931,842.0 269.3 1,840.02,082.2 189 60.00 2.242 0.075 2.6 06/06/09 32,834,352.8 271.9 1,840.02,248.4 210 60.00 2.369 0.085 2.6 06/06/09 32,451,581.7 268.9 1,840.02,292.8 205 60.00 2.296 0.084 2.6 06/06/09 30,424,644.9 269.3 1,840.02,116.5 194 60.00 2.332 0.079 2.9 06/06/09 30,618,342.7 271.2 1,840.02,146.6 199 60.00 2.314 0.079 2.3 06/06/09 33,149,403.3 269.6 1,840.02,414.1 219 60.00 2.485 0.096 2.0 06/06/09 28,885,537.1 264.0 1,840.02,056.6 184 60.00 2.016 0.066 1.9 06/06/09 26,475,098.5 264.51,840.0 1,841.7 168 60.00 1.794 0.053 2.0 06/06/09 26,896,708.8 264.9 1,840.0 1,871.1 169 60.00 1.704 0.051 2.0 06/06/09 26,247,838.2 266.0 1,840.0 1,811.7 163 60.00 1.808 0.052 1.9 06/06/09 28,310,236.4 266.4 1,840.02,000.2 180 60.00 1.766 0.056 1.8 06/06/09 27,632,045.7 267.1 1,840.0 1,997.3 185 60.00 1.640 0.052 2.4 06/06/09 29,690,650.1 269.2 1,840.02,146.1 199 60.00 1.554 0.053 2.2 06/06/09 31,785,694.4 268.0 1,840.02,280.3 201 60.00 2.088 0.076 2.4 06/06/09 28,337,401.0 266.0 1,840.0 1,986.7 173 60.00 1.958 0.062 2.5 06/06/09 26,159,273.5 264.0 1,840.0 1,819.8 158 60.00 2.153 0.063 1.6 06/06/09 25,799,761.6 263.2 1,840.0 1,808.8 158 60.00 2.225 0.064 2.0 06/06/09 25,054,957.9 264.0 1,840.0 1,770.2 154 60.00 1.413 0.040 1.8 06/06/09 25,951,964.3 264.6 1,840.0 1,833.6 159 60.00 1.766 0.052 1.9 06/06/09 25,690,591.0 263.8 1,840.0 1,731.3 157 60.00 1.667 0.046 1.9 06/06/09 26,085,967.9 262.51,840.0 1,729.6 158 60.00 1.788 0.049 1.9 06/06/09 25,651,770.5 262.7 1,840.0 1,714.8 157 60.00 1.774 0.049 1.9 06/05/09 25,960,115.4 264.0 1,840.0 1,763.6 158 60.00 1.745 0.049 1.9 06/05/09 26,154,702.4 264.3 1,840.0 1,791.0 158 60.00 1.731 0.050 1.7 06/05/09 25,354,610.9 265.2 1,840.0 1,708.7 155 60.00 1.759 0.048 1.3 06/05/09 28,468,119.7 269.7 1,840.0 1,980.4 178 60.00 1.525 0.048 1.2 06/05/09 30,746,617.5 268.3 1,840.02,155.6 187 60.00 1.157 0.040 1.2 06/05/09 27,736,464.4 269.0 1,840.0 1,929.5 170 60.00 1.076 0.033 06/05/09 30,908,400.1 271.1 1,840.02,150.1 193 60.00 1.076 0.037

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S 03:00 04:00 ST ST ST ST C 05:00 STC ST ST ST C 06:00 ST ST ST ST 07:00 C 08:00 09:00 10:00 11:00 12:00 S S S 13:00 S S S 14:00 15:00 16:00 S S S 17:00 S S S 18:00 2.1 1.9 06/08/09 33,288,649.8 269.8 1,840.02,279.6 208 60.00 1.914 0.070 1.9 06/08/09 34,038,424.0 272.6 1,840.02,423.4 226 60.00 1.665 0.065 1.8 06/08/09 37,928,732.3 273.2 1,840.02,782.8 258 60.00 1.616 0.072 3.2 06/08/09 38,205,330.8 273.3 1,840.02,803.1 259 60.00 1.531 0.069 3.0 06/08/09 37,249,319.1 273.0 1,840.02,692.5 249 60.00 2.762 0.119 3.0 06/08/09 38,087,754.8 273.6 1,840.02,732.4 255 60.00 2.609 0.114 2.8 06/08/09 38,418,999.9 273.3 1,840.02,735.3 254 60.00 2.629 0.115 2.3 06/08/09 37,093,385.8 271.6 1,840.02,661.0 243 60.00 2.435 0.104 2.2 06/08/09 38,353,346.0 272.1 1,840.02,772.3 257 60.00 1.986 0.088 2.0 06/08/09 38,416,991.7 272.0 1,840.02,776.9 257 60.00 1.899 0.084 1.6 06/08/09 37,602,678.0 268.7 1,840.02,718.0 249 60.00 1.727 0.075 1.7 06/08/09 36,181,559.7 265.1 1,840.02,595.7 243 60.00 1.392 0.058 1.4 06/08/09 26,135,000.0 248.3 1,840.0 1,406.2 194 60.00 1.972 0.044 0.8 06/08/09 26,135,000.0 225.3 1,840.0 1,406.2 163 60.00 1.624 0.037 0.5 06/08/09 25,257,000.0 210.9 1,840.0 1,358.9 115 60.00 0.928 0.020 0.0 06/08/09 23,958,321.0 209.7 1,840.0 859.4 54 60.00 0.870 0.012 0.8 06/08/09 25,547,488.6 220.8 1,840.0 1,360.7 0 39.00 0.000 0.000 0.8 06/08/09 24,359,814.4 261.8 1,840.0 1,721.1 150 19.00 0.707 0.006 1.6 06/08/09 24,884,004.0 262.8 1,840.0 1,731.1 151 60.00 0.718 0.020 1.6 06/07/09 25,688,395.2 263.4 1,840.0 1,787.0 155 60.00 1.435 0.041 1.7 06/07/09 25,666,797.9 263.51,840.0 1,827.4 157 60.00 1.402 0.041 1.6 06/07/09 26,127,974.0 264.51,840.0 1,831.8 166 60.00 1.513 0.044 1.4 06/07/09 30,661,130.6 266.8 1,840.02,166.3 196 60.00 1.413 0.049 1.4 06/07/09 28,487,554.6 264.1 1,840.02,012.7 174 60.00 1.236 0.040 1.7 06/07/09 26,240,197.4 264.2 1,840.0 1,811.1 160 60.00 1.266 0.037 1.7 06/07/09 26,242,355.4 263.1 1,840.0 1,854.1 163 60.00 1.501 0.045 1.3 06/07/09 25,907,552.2 262.7 1,840.0 1,802.3 160 60.00 1.525 0.044 1.4 06/07/09 25,934,511.9 263.9 1,840.0 1,790.1 159 60.00 1.175 0.034 1.5 06/07/09 26,269,092.4 264.2 1,840.0 1,813.1 159 60.00 1.266 0.037 2.1 06/07/09 26,438,167.6 264.1 1,840.0 1,824.8 160 60.00 1.356 0.040 2.2 06/07/09 25,955,552.1 263.1 1,840.0 1,791.5 161 60.00 1.899 0.054 2.0 06/07/09 26,197,923.1 262.7 1,840.0 1,808.2 163 60.00 1.989 0.058 1.8 06/07/09 25,804,405.1 263.1 1,840.0 1,767.0 160 60.00 1.822 0.051 1.9 06/07/09 26,105,895.0 263.6 1,840.0 1,773.5 160 60.00 1.653 0.047 2.0 06/07/09 26,392,661.2 263.7 1,840.0 1,778.7 159 60.00 1.759 0.050 2.6 06/07/09 26,089,803.4 263.0 1,840.0 1,772.4 159 60.00 1.837 0.052 06/07/09 25,801,822.9 262.2 1,840.0 1,766.9 160 60.00 2.369 0.067

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 C 15:00 C 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 3.9 3.3 06/10/09 39,781,658.8 278.4 1,840.02,897.2 267 60.00 3.342 0.155 2.3 06/10/09 35,844,088.3 270.6 1,840.02,571.4 232 60.00 2.870 0.118 2.2 06/10/09 28,800,027.8 265.2 1,840.0 1,940.9 172 60.00 2.130 0.066 2.2 06/10/09 25,572,003.6 265.4 1,840.0 1,709.4 153 60.00 2.054 0.056 2.7 06/10/09 26,652,786.9 265.0 1,840.0 1,752.7 158 60.00 2.088 0.059 2.5 06/10/09 26,377,207.3 264.3 1,840.0 1,748.9 161 60.00 2.541 0.071 2.5 06/10/09 25,410,739.9 264.51,840.0 1,740.1 155 60.00 2.278 0.063 2.3 06/10/09 26,476,434.8 267.51,840.0 1,827.4 167 60.00 2.260 0.066 2.0 06/09/09 28,661,576.1 266.51,840.0 1,962.7 175 60.00 2.096 0.066 2.0 06/09/09 26,862,460.8 267.7 1,840.0 1,810.3 163 60.00 1.852 0.054 2.2 06/09/09 29,223,620.3 271.0 1,840.02,017.1 184 60.00 1.808 0.058 1.8 06/09/09 31,717,111.2 270.9 1,840.02,240.9 204 60.00 1.943 0.070 2.4 06/09/09 30,744,822.4 268.51,840.02,188.9 194 60.00 1.578 0.055 2.7 06/09/09 27,437,657.1 269.2 1,840.0 1,908.7 170 60.00 2.153 0.066 2.3 06/09/09 29,808,867.7 272.8 1,840.02,041.3 184 60.00 2.460 0.080 2.1 06/09/09 35,825,107.9 281.51,840.02,570.1 240 60.00 2.001 0.082 2.9 06/09/09 38,503,060.4 281.8 1,840.02,804.0 260 60.00 1.799 0.081 2.8 06/09/09 39,960,312.4 282.6 1,840.02,931.8 272 60.00 2.466 0.116 2.5 06/09/09 39,723,934.2 281.51,840.02,892.9 270 60.00 2.399 0.111 2.7 06/09/09 39,070,352.4 279.51,840.02,824.1 265 60.00 2.158 0.097 2.5 06/09/09 39,510,745.7 280.4 1,840.02,877.4 268 60.00 2.313 0.106 2.1 06/09/09 39,368,729.4 279.51,840.02,888.5 269 60.00 2.126 0.098 2.1 06/09/09 39,953,643.2 280.4 1,840.02,953.1 273 60.00 1.773 0.084 2.1 06/09/09 39,647,581.0 279.9 1,840.02,952.1 273 60.00 1.760 0.083 2.0 06/09/09 39,865,671.2 279.3 1,840.02,925.0 272 60.00 1.786 0.084 1.6 06/09/09 39,539,011.0 276.8 1,840.02,901.0 271 60.00 1.701 0.079 1.1 06/09/09 35,600,342.6 269.3 1,840.02,515.2 228 60.00 1.413 0.057 1.3 06/09/09 28,646,582.6 264.7 1,840.0 1,961.7 174 60.00 1.002 0.031 1.5 06/09/09 25,692,633.0 263.8 1,840.0 1,759.4 156 60.00 1.185 0.033 1.5 06/09/09 24,752,034.7 264.2 1,840.0 1,695.0 152 60.00 1.367 0.037 1.8 06/09/09 25,112,603.5 264.8 1,840.0 1,706.0 151 60.00 1.378 0.038 2.0 06/09/09 26,477,860.7 266.51,840.0 1,798.8 162 60.00 1.653 0.048 2.0 06/08/09 29,761,208.3 268.1 1,840.02,005.6 186 60.00 1.852 0.059 2.1 06/08/09 29,337,299.3 269.2 1,840.0 1,993.0 183 60.00 1.837 0.059 2.3 06/08/09 31,995,901.0 272.7 1,840.02,173.6 201 60.00 1.929 0.067 2.2 06/08/09 37,274,244.8 275.6 1,840.02,613.2 242 60.00 2.047 0.086 06/08/09 34,886,004.2 272.4 1,840.02,445.8 225 60.00 1.958 0.077

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 3.9 3.6 06/11/09 37,459,750.9 278.0 1,840.02,646.6 250 60.00 3.444 0.146 3.9 06/11/09 33,234,303.0 275.0 1,840.02,366.1 221 60.00 3.155 0.119 4.5 06/11/09 33,920,233.0 277.3 1,840.02,378.1 225 60.00 3.471 0.132 4.6 06/11/09 38,317,665.5 280.51,840.02,707.3 258 60.00 3.974 0.172 4.4 06/11/09 39,790,632.3 281.0 1,840.02,854.6 271 60.00 4.001 0.183 4.1 06/11/09 39,485,152.7 277.3 1,840.02,746.8 262 60.00 3.947 0.173 4.1 06/11/09 36,373,445.2 276.51,840.02,510.5 238 60.00 3.707 0.149 3.9 06/11/09 36,118,606.3 276.6 1,840.02,532.3 238 60.00 3.649 0.148 3.6 06/11/09 36,045,014.1 276.0 1,840.02,546.7 238 60.00 3.444 0.140 3.6 06/11/09 35,862,944.1 277.0 1,840.02,514.3 238 60.00 3.204 0.129 3.6 06/11/09 36,152,592.9 277.6 1,840.02,534.6 238 60.00 3.204 0.130 4.0 06/11/09 36,289,340.2 278.0 1,840.02,544.2 238 60.00 3.204 0.130 4.1 06/11/09 35,970,866.5 277.7 1,840.02,541.4 238 60.00 3.533 0.144 4.2 06/11/09 35,577,631.0 277.1 1,840.02,533.0 238 60.00 3.593 0.146 3.9 06/11/09 35,394,016.4 276.3 1,840.02,539.1 238 60.00 3.653 0.148 2.4 06/11/09 35,290,472.0 274.9 1,840.02,550.9 238 60.00 3.367 0.137 2.2 06/11/09 33,034,776.0 268.8 1,840.02,334.0 210 60.00 2.120 0.079 2.4 06/11/09 26,162,218.7 266.1 1,840.0 1,748.9 160 60.00 2.054 0.057 3.0 06/11/09 26,285,848.9 265.6 1,840.0 1,728.6 160 60.00 2.277 0.063 3.0 06/11/09 25,182,245.2 265.7 1,840.0 1,669.7 156 60.00 2.823 0.075 2.9 06/11/09 27,060,848.3 265.9 1,840.0 1,794.3 166 60.00 2.823 0.081 3.3 06/10/09 26,899,747.8 270.2 1,840.0 1,769.0 167 60.00 2.752 0.078 3.9 06/10/09 31,303,170.4 276.2 1,840.02,143.6 208 60.00 3.007 0.103 4.2 06/10/09 37,309,587.3 279.6 1,840.02,636.0 249 60.00 3.444 0.145 4.0 06/10/09 38,922,075.5 281.3 1,840.02,771.1 263 60.00 3.681 0.163 4.2 06/10/09 40,258,954.3 282.2 1,840.02,800.6 268 60.00 3.588 0.161 4.3 06/10/09 39,620,664.6 283.2 1,840.02,756.2 264 60.00 3.767 0.166 4.5 06/10/09 39,884,024.1 284.0 1,840.02,817.9 269 60.00 3.798 0.171 4.1 06/10/09 40,446,306.3 283.51,840.02,857.6 272 60.00 3.974 0.182 4.5 06/10/09 40,327,344.7 281.7 1,840.02,849.2 271 60.00 3.621 0.165 4.4 06/10/09 40,305,155.1 282.1 1,840.02,847.6 270 60.00 3.974 0.181 4.3 06/10/09 40,521,273.0 281.9 1,840.02,906.9 269 60.00 3.827 0.178 4.3 06/10/09 40,088,950.5 281.7 1,840.02,876.0 268 60.00 3.740 0.172 3.9 06/10/09 40,536,423.2 280.2 1,840.02,908.0 271 60.00 3.740 0.174 3.7 06/10/09 38,853,795.4 278.3 1,840.02,808.5 258 60.00 3.367 0.151 3.8 06/10/09 37,055,101.2 278.7 1,840.02,698.6 248 60.00 3.170 0.137 06/10/09 38,828,667.7 280.6 1,840.02,848.9 262 60.00 3.232 0.147

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 2.6 2.6 06/13/09 33,765,328.6 270.2 1,840.02,422.3 213 60.00 2.262 0.088 3.0 06/13/09 29,719,753.3 272.7 1,840.02,164.4 194 60.00 2.228 0.077 2.3 06/13/09 35,378,768.1 270.3 1,840.02,499.6 223 60.00 2.650 0.106 2.2 06/13/09 28,531,012.2 267.51,840.02,000.3 179 60.00 2.047 0.065 2.1 06/13/09 27,027,590.7 266.1 1,840.0 1,880.2 164 60.00 1.973 0.059 2.2 06/13/09 26,217,293.1 265.4 1,840.0 1,795.3 158 60.00 1.914 0.055 2.2 06/13/09 24,538,944.7 265.2 1,840.0 1,707.1 151 60.00 1.973 0.054 2.1 06/13/09 26,158,793.6 265.8 1,840.0 1,762.9 157 60.00 2.037 0.057 2.3 06/13/09 25,362,513.8 266.3 1,840.0 1,750.6 153 60.00 1.899 0.053 2.8 06/13/09 25,160,586.1 266.3 1,840.0 1,750.3 154 60.00 2.063 0.058 3.1 06/12/09 25,336,116.6 266.7 1,840.0 1,748.7 156 60.00 2.531 0.071 3.5 06/12/09 27,214,720.0 270.6 1,840.0 1,893.2 172 60.00 2.781 0.084 3.9 06/12/09 33,929,123.2 274.51,840.02,341.8 214 60.00 3.164 0.118 3.3 06/12/09 35,257,498.3 273.3 1,840.02,452.7 222 60.00 3.498 0.137 3.5 06/12/09 30,585,845.6 267.2 1,840.02,044.6 181 60.00 3.080 0.101 3.7 06/12/09 28,504,899.4 269.2 1,840.0 1,874.5 173 60.00 3.321 0.100 3.9 06/12/09 31,945,251.9 274.51,840.02,152.8 202 60.00 3.426 0.118 4.2 06/12/09 36,560,478.1 277.2 1,840.02,583.0 238 60.00 3.444 0.142 4.1 06/12/09 39,533,461.4 279.2 1,840.02,814.6 262 60.00 3.681 0.166 3.2 06/12/09 39,899,527.6 278.6 1,840.02,840.7 262 60.00 3.593 0.163 1.4 06/12/09 39,254,718.9 276.51,840.02,752.1 253 60.00 2.848 0.125 1.9 06/12/09 37,853,333.4 274.9 1,840.02,530.4 238 60.00 1.307 0.053 3.1 06/12/09 36,854,007.2 274.9 1,840.02,523.7 238 60.00 1.731 0.070 3.2 06/12/09 36,916,715.2 275.2 1,840.02,528.0 238 60.00 2.825 0.114 2.6 06/12/09 36,470,906.7 275.0 1,840.02,556.9 238 60.00 2.848 0.116 2.6 06/12/09 33,443,524.7 267.9 1,840.02,381.1 213 60.00 2.279 0.087 2.5 06/12/09 24,936,789.4 264.3 1,840.0 1,748.3 158 60.00 2.314 0.065 2.2 06/12/09 24,811,890.9 264.3 1,840.0 1,753.0 159 60.00 2.208 0.062 2.2 06/12/09 25,228,362.1 265.2 1,840.0 1,768.7 159 60.00 1.958 0.055 2.3 06/12/09 25,250,751.2 265.6 1,840.0 1,756.6 158 60.00 1.973 0.055 2.7 06/12/09 25,243,602.7 265.3 1,840.0 1,728.7 156 60.00 2.096 0.058 2.9 06/12/09 24,510,598.2 264.1 1,840.0 1,678.5 155 60.00 2.460 0.066 2.9 06/12/09 24,328,236.9 264.8 1,840.0 1,679.2 152 60.00 2.622 0.070 3.0 06/12/09 24,861,383.4 265.9 1,840.0 1,675.4 152 60.00 2.685 0.072 3.1 06/11/09 26,179,863.5 268.1 1,840.0 1,735.8 160 60.00 2.823 0.078 4.0 06/11/09 28,783,695.4 273.7 1,840.0 1,986.7 187 60.00 2.803 0.089 06/11/09 36,240,546.7 278.51,840.02,580.2 246 60.00 3.506 0.145

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 3.0 3.6 06/14/09 29,031,625.4 272.3 1,840.02,114.3 192 60.00 2.571 0.087 4.0 06/14/09 34,828,915.2 277.1 1,840.02,479.7 229 60.00 3.155 0.125 3.5 06/14/09 38,199,054.2 278.7 1,840.02,698.8 249 60.00 3.533 0.152 4.0 06/14/09 36,462,956.9 276.51,840.02,576.2 234 60.00 3.091 0.127 4.4 06/14/09 35,668,729.1 278.0 1,840.02,520.1 233 60.00 3.533 0.142 4.3 06/14/09 38,826,678.3 279.2 1,840.02,764.3 257 60.00 3.856 0.170 4.4 06/14/09 38,637,921.1 279.7 1,840.02,729.9 254 60.00 3.798 0.166 4.4 06/14/09 40,160,210.1 280.2 1,840.02,815.6 260 60.00 3.916 0.176 4.2 06/14/09 39,836,453.0 280.9 1,840.02,771.2 258 60.00 3.947 0.175 4.5 06/14/09 39,873,866.3 282.2 1,840.02,817.2 262 60.00 3.709 0.167 4.5 06/14/09 40,201,846.0 281.8 1,840.02,884.1 267 60.00 3.914 0.181 4.3 06/14/09 40,840,076.9 280.3 1,840.02,863.2 267 60.00 4.005 0.183 4.1 06/14/09 39,900,566.7 277.7 1,840.02,710.7 255 60.00 3.950 0.171 3.8 06/14/09 39,980,268.7 277.51,840.02,650.8 248 60.00 3.859 0.164 3.8 06/14/09 35,528,761.6 274.6 1,840.02,490.9 224 60.00 3.382 0.135 3.7 06/14/09 31,312,251.0 271.2 1,840.02,229.3 198 60.00 3.331 0.119 3.6 06/14/09 28,054,721.6 265.9 1,840.0 1,936.4 170 60.00 3.345 0.104 3.3 06/14/09 25,538,409.6 265.8 1,840.0 1,762.7 157 60.00 3.255 0.092 3.4 06/14/09 24,788,950.6 266.2 1,840.0 1,724.5 152 60.00 2.960 0.082 3.6 06/14/09 25,268,993.5 266.4 1,840.0 1,702.9 152 60.00 3.148 0.086 3.5 06/14/09 25,378,807.0 265.7 1,840.0 1,668.9 153 60.00 3.416 0.091 3.5 06/14/09 24,995,444.0 265.1 1,840.0 1,684.4 152 60.00 3.241 0.087 3.5 06/14/09 25,032,085.1 265.7 1,840.0 1,686.9 153 60.00 3.241 0.087 3.9 06/13/09 26,544,583.6 270.2 1,840.0 1,803.3 166 60.00 3.215 0.093 4.1 06/13/09 30,575,328.0 272.7 1,840.02,110.3 191 60.00 3.526 0.119 3.8 06/13/09 32,474,601.2 273.6 1,840.02,294.4 206 60.00 3.621 0.133 3.3 06/13/09 32,095,370.8 271.4 1,840.02,285.0 204 60.00 3.331 0.122 3.3 06/13/09 27,218,646.9 266.2 1,840.0 1,849.1 167 60.00 3.031 0.090 3.5 06/13/09 26,503,627.6 267.6 1,840.0 1,771.7 162 60.00 3.080 0.087 4.0 06/13/09 29,077,657.3 272.3 1,840.0 1,975.4 184 60.00 3.215 0.102 3.8 06/13/09 34,340,812.6 274.7 1,840.02,444.9 222 60.00 3.506 0.137 3.4 06/13/09 33,025,837.6 271.7 1,840.02,297.5 207 60.00 3.409 0.125 3.6 06/13/09 30,645,851.8 270.1 1,840.02,081.9 188 60.00 3.123 0.104 3.7 06/13/09 31,329,720.2 272.0 1,840.02,179.5 198 60.00 3.229 0.113 3.6 06/13/09 32,805,887.1 273.6 1,840.02,317.8 211 60.00 3.268 0.121 3.3 06/13/09 33,824,141.3 271.1 1,840.02,408.1 216 60.00 3.155 0.121 06/13/09 32,682,898.3 273.4 1,840.02,344.7 215 60.00 2.870 0.108

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 4.4 4.2 06/16/09 32,018,230.1 273.7 1,840.02,296.9 204 60.00 3.827 0.141 4.0 06/16/09 30,887,274.4 269.6 1,840.02,199.0 192 60.00 3.681 0.129 4.1 06/16/09 28,505,161.2 267.6 1,840.0 1,998.4 176 60.00 3.560 0.114 3.8 06/16/09 27,946,648.8 269.0 1,840.0 1,944.1 176 60.00 3.678 0.114 4.2 06/16/09 29,408,157.4 270.9 1,840.02,029.8 182 60.00 3.435 0.112 4.5 06/16/09 32,740,952.7 272.2 1,840.02,366.6 211 60.00 3.626 0.137 4.6 06/16/09 29,158,986.6 266.7 1,840.02,012.6 177 60.00 4.068 0.131 4.1 06/16/09 26,204,048.7 264.51,840.0 1,723.2 156 60.00 4.365 0.120 4.2 06/16/09 25,756,331.9 265.4 1,840.0 1,679.7 152 60.00 3.923 0.105 4.2 06/16/09 25,726,313.3 265.6 1,840.0 1,677.8 151 60.00 4.019 0.108 4.2 06/16/09 26,111,075.3 265.6 1,840.0 1,688.7 151 60.00 4.052 0.109 4.2 06/16/09 25,605,634.7 265.0 1,840.0 1,697.8 151 60.00 3.953 0.107 3.8 06/15/09 25,629,271.6 264.51,840.0 1,699.3 153 60.00 3.953 0.107 3.0 06/15/09 25,359,940.2 264.51,840.0 1,695.3 152 60.00 3.547 0.096 2.5 06/15/09 27,767,137.9 266.3 1,840.0 1,841.1 167 60.00 2.823 0.083 4.0 06/15/09 25,175,390.9 269.7 1,840.0 1,860.8 162 60.00 2.111 0.063 4.5 06/15/09 28,850,834.3 272.51,840.02,022.7 184 60.00 3.560 0.115 4.7 06/15/09 34,145,840.7 276.6 1,840.02,356.8 219 60.00 4.068 0.153 4.7 06/15/09 35,815,617.0 275.7 1,840.02,608.3 235 60.00 4.027 0.168 5.1 06/15/09 36,896,043.4 279.3 1,840.02,626.8 245 60.00 4.119 0.173 4.9 06/15/09 40,311,070.1 279.7 1,840.02,913.8 269 60.00 4.403 0.205 4.9 06/15/09 39,992,031.6 280.4 1,840.02,847.3 264 60.00 4.295 0.196 4.9 06/15/09 40,596,245.5 280.6 1,840.02,890.3 268 60.00 4.295 0.198 4.6 06/15/09 40,482,570.6 280.4 1,840.02,882.2 268 60.00 4.295 0.198 4.0 06/15/09 40,275,900.7 279.1 1,840.02,867.5 267 60.00 4.032 0.185 3.6 06/15/09 40,507,004.2 277.8 1,840.02,905.9 270 60.00 3.479 0.162 3.4 06/15/09 38,910,686.9 277.2 1,840.02,791.4 258 60.00 3.131 0.140 3.1 06/15/09 37,481,414.6 275.8 1,840.02,688.9 244 60.00 2.957 0.127 2.7 06/15/09 37,929,202.6 276.7 1,840.02,741.6 250 60.00 2.676 0.117 2.4 06/15/09 35,298,902.1 270.6 1,840.02,532.3 224 60.00 2.349 0.095 2.2 06/15/09 26,781,065.4 265.3 1,840.0 1,892.1 167 60.00 2.120 0.064 2.2 06/15/09 25,809,475.4 265.8 1,840.0 1,781.4 159 60.00 1.989 0.057 2.3 06/15/09 25,882,456.0 266.1 1,840.0 1,758.3 156 60.00 2.021 0.057 2.7 06/15/09 25,368,002.8 265.7 1,840.0 1,709.6 153 60.00 2.130 0.058 2.8 06/15/09 24,636,766.9 265.7 1,840.0 1,713.9 153 60.00 2.422 0.066 2.9 06/15/09 25,413,107.2 266.2 1,840.0 1,767.9 158 60.00 2.512 0.071 06/14/09 24,873,964.0 268.4 1,840.0 1,730.4 157 60.00 2.601 0.072

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 2.4 2.5 06/18/09 24,914,083.3 266.0 1,840.0 1,746.7 152 60.00 2.136 0.060 3.1 06/17/09 24,948,561.9 268.7 1,840.0 1,735.6 153 60.00 2.242 0.062 3.3 06/17/09 30,364,384.8 274.3 1,840.02,145.3 199 60.00 2.738 0.094 3.3 06/17/09 36,442,833.1 275.9 1,840.02,654.0 245 60.00 2.828 0.120 3.3 06/17/09 37,464,840.1 277.4 1,840.02,728.4 251 60.00 2.828 0.123 3.4 06/17/09 37,096,908.8 277.0 1,840.02,681.5 247 60.00 2.849 0.122 3.6 06/17/09 37,161,148.8 277.6 1,840.02,686.1 248 60.00 2.935 0.126 3.8 06/17/09 39,289,832.9 280.4 1,840.02,882.7 268 60.00 3.062 0.141 3.9 06/17/09 40,108,140.4 280.8 1,840.02,942.7 273 60.00 3.232 0.152 4.0 06/17/09 40,437,382.7 280.7 1,840.02,944.9 273 60.00 3.342 0.157 3.9 06/17/09 40,259,173.8 280.4 1,840.02,953.8 273 60.00 3.402 0.161 4.1 06/17/09 40,174,431.6 280.7 1,840.02,947.5 273 60.00 3.317 0.156 4.1 06/17/09 40,384,250.5 280.9 1,840.02,941.0 273 60.00 3.513 0.165 4.2 06/17/09 40,458,283.0 280.6 1,840.02,946.4 272 60.00 3.513 0.166 4.1 06/17/09 39,863,800.0 278.4 1,840.02,903.1 268 60.00 3.599 0.167 3.9 06/17/09 38,079,301.8 277.0 1,840.02,773.1 255 60.00 3.513 0.156 3.8 06/17/09 38,979,159.0 276.51,840.02,817.5 261 60.00 3.367 0.152 3.5 06/17/09 39,481,198.5 276.9 1,840.02,832.3 262 60.00 3.305 0.150 2.8 06/17/09 36,746,878.1 273.6 1,840.02,676.1 240 60.00 2.999 0.128 2.6 06/17/09 31,037,454.1 266.9 1,840.02,243.4 195 60.00 2.417 0.087 2.6 06/17/09 25,651,316.4 264.1 1,840.0 1,784.4 158 60.00 2.332 0.067 2.7 06/17/09 25,412,563.1 264.4 1,840.0 1,767.9 156 60.00 2.332 0.066 2.8 06/17/09 24,899,801.0 265.6 1,840.0 1,678.0 152 60.00 2.500 0.067 3.1 06/17/09 25,440,443.1 266.4 1,840.0 1,755.9 154 60.00 2.531 0.071 3.0 06/17/09 26,496,455.8 268.1 1,840.0 1,828.8 164 60.00 2.803 0.082 3.2 06/16/09 27,519,879.7 267.3 1,840.0 1,944.3 173 60.00 2.650 0.082 3.7 06/16/09 27,051,516.4 272.8 1,840.0 1,896.6 177 60.00 2.848 0.086 4.0 06/16/09 35,294,403.6 277.2 1,840.02,589.5 236 60.00 3.147 0.130 4.0 06/16/09 37,714,219.4 279.1 1,840.02,726.1 253 60.00 3.453 0.151 4.2 06/16/09 38,604,397.3 279.51,840.02,811.4 260 60.00 3.427 0.154 4.2 06/16/09 38,320,149.7 278.4 1,840.02,790.7 260 60.00 3.599 0.161 4.2 06/16/09 39,721,855.1 280.4 1,840.02,914.4 270 60.00 3.572 0.166 4.1 06/16/09 39,106,334.8 279.3 1,840.02,847.9 262 60.00 3.599 0.164 3.7 06/16/09 37,917,200.5 277.4 1,840.02,740.7 248 60.00 3.539 0.155 3.7 06/16/09 32,536,347.6 271.6 1,840.02,351.8 207 60.00 3.194 0.120 3.9 06/16/09 30,754,949.4 272.0 1,840.02,206.3 197 60.00 3.218 0.114 06/16/09 31,106,644.3 272.1 1,840.02,231.6 196 60.00 3.392 0.121

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 5.1 5.2 06/19/09 39,943,173.7 282.2 1,840.02,843.8 268 60.00 4.470 0.203 5.2 06/19/09 40,672,834.5 283.2 1,840.02,895.7 271 60.00 4.558 0.211 5.2 06/19/09 40,587,916.1 283.2 1,840.02,911.7 272 60.00 4.523 0.211 4.6 06/19/09 40,709,165.7 281.7 1,840.02,898.3 271 60.00 4.558 0.211 4.5 06/19/09 39,008,620.8 281.2 1,840.02,777.3 261 60.00 4.032 0.179 4.8 06/19/09 40,551,124.7 282.51,840.02,887.1 273 60.00 3.944 0.182 4.7 06/19/09 40,171,650.5 280.7 1,840.02,860.1 267 60.00 4.207 0.192 4.6 06/19/09 38,468,191.8 277.8 1,840.02,717.8 252 60.00 4.151 0.180 3.5 06/19/09 34,555,046.8 271.9 1,840.02,460.2 222 60.00 4.032 0.159 3.3 06/19/09 29,459,762.0 268.3 1,840.02,081.4 178 60.00 3.091 0.103 3.7 06/19/09 25,835,515.8 270.3 1,840.0 1,797.3 158 60.00 2.960 0.085 3.5 06/19/09 30,157,279.9 270.6 1,840.02,065.1 185 60.00 3.372 0.111 3.8 06/19/09 28,631,217.3 270.6 1,840.0 1,991.7 178 60.00 3.139 0.100 3.9 06/19/09 32,403,549.7 275.3 1,840.02,271.8 210 60.00 3.382 0.123 4.1 06/18/09 35,775,991.9 279.1 1,840.02,547.1 235 60.00 3.418 0.139 4.1 06/18/09 37,988,081.1 281.3 1,840.02,745.9 254 60.00 3.539 0.155 4.0 06/18/09 39,153,188.7 283.0 1,840.02,872.6 266 60.00 3.487 0.160 3.7 06/18/09 39,451,747.8 282.6 1,840.02,916.0 272 60.00 3.377 0.157 3.6 06/18/09 39,473,136.5 281.6 1,840.02,939.0 272 60.00 3.101 0.146 3.3 06/18/09 39,319,831.7 280.8 1,840.02,906.3 271 60.00 3.039 0.141 3.4 06/18/09 39,518,951.2 282.0 1,840.02,921.0 272 60.00 2.786 0.130 3.4 06/18/09 39,857,056.3 282.0 1,840.02,946.0 273 60.00 2.870 0.135 3.7 06/18/09 39,948,337.8 282.0 1,840.02,909.3 273 60.00 2.913 0.136 3.8 06/18/09 39,689,099.0 281.51,840.02,912.0 273 60.00 3.147 0.147 3.7 06/18/09 39,585,907.0 281.0 1,840.02,925.9 273 60.00 3.208 0.150 3.6 06/18/09 39,394,681.3 280.7 1,840.02,933.2 273 60.00 3.101 0.145 3.4 06/18/09 39,515,313.1 278.9 1,840.02,942.1 271 60.00 3.017 0.142 3.5 06/18/09 38,770,831.5 278.6 1,840.02,844.6 261 60.00 2.892 0.132 3.5 06/18/09 36,810,185.4 275.6 1,840.02,660.7 241 60.00 3.021 0.129 3.8 06/18/09 33,621,547.3 274.3 1,840.02,393.7 216 60.00 3.068 0.117 3.7 06/18/09 34,378,658.2 273.8 1,840.02,485.0 225 60.00 3.280 0.130 3.1 06/18/09 34,811,013.3 271.7 1,840.02,516.2 227 60.00 3.194 0.129 2.4 06/18/09 31,118,392.7 265.9 1,840.02,232.4 198 60.00 2.696 0.096 2.2 06/18/09 25,648,455.2 265.2 1,840.0 1,784.2 159 60.00 2.153 0.061 2.2 06/18/09 26,226,847.1 264.8 1,840.0 1,824.5 160 60.00 1.973 0.058 2.4 06/18/09 24,887,945.9 264.51,840.0 1,690.8 151 60.00 2.021 0.055 06/18/09 24,805,285.8 264.6 1,840.0 1,739.0 153 60.00 2.136 0.059

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 4.1 3.8 06/21/09 31,238,932.4 270.6 1,840.02,105.2 192 60.00 3.796 0.128 4.0 06/21/09 30,544,300.7 272.51,840.02,075.0 191 60.00 3.490 0.116 4.3 06/21/09 34,705,869.9 275.4 1,840.02,357.7 220 60.00 3.674 0.139 4.2 06/20/09 35,388,615.5 276.9 1,840.02,423.4 226 60.00 3.918 0.152 3.8 06/20/09 35,233,785.2 275.7 1,840.02,470.2 223 60.00 3.738 0.148 4.1 06/20/09 34,129,920.6 277.8 1,840.02,411.4 225 60.00 3.356 0.129 4.2 06/20/09 39,806,447.6 280.2 1,840.02,855.6 263 60.00 3.566 0.163 4.4 06/20/09 38,179,828.4 280.51,840.02,718.3 251 60.00 3.681 0.160 4.4 06/20/09 38,194,673.6 281.3 1,840.02,719.3 251 60.00 3.856 0.168 4.4 06/20/09 38,265,627.1 279.8 1,840.02,745.2 249 60.00 3.827 0.168 4.1 06/20/09 35,897,112.8 277.51,840.02,575.2 233 60.00 3.827 0.158 4.1 06/20/09 33,679,908.4 275.6 1,840.02,397.9 218 60.00 3.593 0.138 3.6 06/20/09 34,239,367.7 275.0 1,840.02,456.3 223 60.00 3.566 0.140 3.6 06/20/09 32,347,806.1 272.2 1,840.02,320.6 206 60.00 3.131 0.116 3.4 06/20/09 32,705,962.8 274.4 1,840.02,293.0 207 60.00 3.204 0.117 4.0 06/20/09 32,017,259.6 276.6 1,840.02,262.1 206 60.00 3.003 0.109 4.4 06/20/09 36,813,389.6 279.6 1,840.02,600.9 239 60.00 3.533 0.147 4.7 06/20/09 37,973,806.2 279.9 1,840.02,703.6 247 60.00 3.856 0.167 4.7 06/20/09 36,668,018.7 279.4 1,840.02,610.6 239 60.00 4.119 0.172 4.1 06/20/09 38,496,888.9 278.0 1,840.02,782.7 251 60.00 4.057 0.181 3.2 06/20/09 32,518,162.8 269.1 1,840.02,279.8 201 60.00 3.649 0.133 2.9 06/20/09 25,840,068.2 265.51,840.0 1,797.6 158 60.00 2.870 0.083 2.9 06/20/09 25,485,403.4 265.51,840.0 1,717.5 154 60.00 2.685 0.074 2.6 06/20/09 25,300,093.3 265.4 1,840.0 1,705.0 153 60.00 2.685 0.073 3.0 06/20/09 26,139,860.6 266.7 1,840.0 1,761.6 160 60.00 2.407 0.068 3.0 06/20/09 25,416,319.3 267.4 1,840.0 1,699.0 151 60.00 2.800 0.076 3.5 06/20/09 27,248,507.8 271.51,840.0 1,806.7 165 60.00 2.823 0.082 3.8 06/19/09 32,004,650.4 272.6 1,840.02,209.0 199 60.00 3.164 0.112 4.2 06/19/09 31,479,077.5 274.1 1,840.02,172.7 199 60.00 3.435 0.119 3.5 06/19/09 34,634,998.2 274.7 1,840.02,428.2 221 60.00 3.738 0.145 4.1 06/19/09 31,762,389.9 274.4 1,840.02,209.5 202 60.00 3.139 0.111 4.3 06/19/09 33,316,860.8 278.51,840.02,335.8 216 60.00 3.649 0.136 4.3 06/19/09 35,681,608.2 278.7 1,840.02,521.0 231 60.00 3.798 0.153 4.6 06/19/09 36,895,158.4 282.7 1,840.02,606.7 245 60.00 3.798 0.158 4.6 06/19/09 39,734,148.4 283.9 1,840.02,850.5 269 60.00 4.001 0.182 4.7 06/19/09 40,007,823.7 282.6 1,840.02,891.9 270 60.00 3.971 0.184 06/19/09 38,990,287.0 281.4 1,840.02,775.9 259 60.00 4.119 0.183

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 3.3 3.4 06/22/09 39,581,800.6 281.8 1,840.02,968.7 270 60.00 2.746 0.130 3.4 06/22/09 39,601,851.0 281.6 1,840.02,948.6 268 60.00 2.849 0.134 3.6 06/22/09 39,368,998.2 281.4 1,840.02,931.3 268 60.00 2.849 0.134 3.7 06/22/09 39,140,315.3 280.3 1,840.02,935.5 268 60.00 2.995 0.141 3.7 06/22/09 39,365,867.8 280.0 1,840.02,931.1 267 60.00 3.101 0.145 3.5 06/22/09 39,980,197.3 279.8 1,840.02,911.6 266 60.00 3.170 0.148 3.8 06/22/09 39,126,738.0 278.3 1,840.02,806.9 256 60.00 3.044 0.137 4.0 06/22/09 39,494,629.4 278.8 1,840.02,833.3 263 60.00 3.305 0.150 3.8 06/22/09 39,887,232.2 278.7 1,840.02,883.1 267 60.00 3.453 0.159 3.5 06/22/09 40,146,736.5 277.8 1,840.02,858.3 263 60.00 3.331 0.152 2.9 06/22/09 37,499,805.6 273.7 1,840.02,629.1 236 60.00 3.115 0.131 3.3 06/22/09 30,273,820.6 267.3 1,840.02,122.5 183 60.00 2.581 0.088 3.3 06/22/09 25,352,052.4 265.6 1,840.0 1,736.1 152 60.00 3.007 0.083 3.8 06/22/09 25,306,729.3 267.6 1,840.0 1,705.5 151 60.00 3.056 0.083 3.8 06/22/09 26,480,261.9 270.3 1,840.0 1,798.9 158 60.00 3.490 0.100 4.4 06/22/09 32,018,393.5 274.4 1,840.02,175.1 199 60.00 3.490 0.121 3.8 06/21/09 34,952,191.7 274.2 1,840.02,412.4 220 60.00 3.978 0.153 4.1 06/21/09 31,820,689.8 272.3 1,840.02,213.6 200 60.00 3.409 0.121 4.4 06/21/09 34,428,628.7 277.1 1,840.02,357.6 220 60.00 3.736 0.141 4.5 06/21/09 38,205,760.2 279.2 1,840.02,637.0 248 60.00 3.978 0.168 4.6 06/21/09 37,871,790.9 277.4 1,840.02,634.6 244 60.00 4.037 0.170 4.4 06/21/09 36,558,477.1 276.1 1,840.02,543.2 236 60.00 4.126 0.168 4.5 06/21/09 36,599,884.5 274.9 1,840.02,546.1 237 60.00 3.947 0.161 4.4 06/21/09 36,326,701.1 275.3 1,840.02,507.4 230 60.00 4.068 0.163 3.8 06/21/09 33,614,843.2 270.9 1,840.02,320.2 205 60.00 3.978 0.148 3.1 06/21/09 30,862,594.0 267.9 1,840.02,130.2 184 60.00 3.435 0.117 3.3 06/21/09 27,044,371.1 266.9 1,840.0 1,866.6 163 60.00 2.803 0.084 3.6 06/21/09 26,183,388.0 266.7 1,840.0 1,778.7 155 60.00 3.031 0.086 3.7 06/21/09 26,692,838.2 266.0 1,840.0 1,769.9 155 60.00 3.388 0.096 3.5 06/21/09 26,228,687.7 266.51,840.0 1,696.3 154 60.00 3.570 0.097 4.2 06/21/09 27,736,463.8 275.1 1,840.0 1,854.1 174 60.00 3.267 0.097 3.8 06/21/09 36,872,220.0 278.2 1,840.02,625.1 238 60.00 3.681 0.155 3.6 06/21/09 36,517,126.2 274.4 1,840.02,580.0 229 60.00 3.356 0.138 3.5 06/21/09 29,292,360.6 267.9 1,840.0 1,989.9 178 60.00 3.307 0.105 3.7 06/21/09 26,501,640.9 266.6 1,840.0 1,786.0 159 60.00 3.241 0.093 3.8 06/21/09 25,588,513.5 266.7 1,840.0 1,710.6 153 60.00 3.454 0.094 06/21/09 26,190,386.5 268.9 1,840.0 1,722.3 159 60.00 3.606 0.099

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 5.3 5.1 06/24/09 33,120,684.4 273.0 1,840.02,340.1 214 60.00 4.681 0.175 5.0 06/24/09 34,191,733.2 274.0 1,840.02,452.9 223 60.00 4.436 0.174 5.7 06/24/09 34,742,841.5 273.9 1,840.02,398.0 219 60.00 4.520 0.173 5.7 06/24/09 34,433,286.6 276.9 1,840.02,432.8 224 60.00 5.034 0.196 6.3 06/24/09 38,048,823.4 279.2 1,840.02,708.9 254 60.00 4.996 0.216 6.5 06/23/09 40,036,227.5 280.6 1,840.02,915.7 272 60.00 5.398 0.252 6.3 06/23/09 40,291,971.2 279.9 1,840.02,912.4 273 60.00 5.611 0.261 6.3 06/23/09 40,098,203.0 279.8 1,840.02,898.4 271 60.00 5.439 0.252 6.3 06/23/09 40,264,871.2 280.4 1,840.02,910.5 273 60.00 5.439 0.253 6.1 06/23/09 40,360,098.1 280.4 1,840.02,917.3 272 60.00 5.439 0.254 6.1 06/23/09 40,259,701.9 279.8 1,840.02,866.3 269 60.00 5.346 0.245 5.7 06/23/09 39,884,813.5 278.7 1,840.02,861.3 268 60.00 5.306 0.243 5.3 06/23/09 39,924,932.1 279.9 1,840.02,864.2 267 60.00 4.958 0.227 5.3 06/23/09 40,101,430.4 279.9 1,840.02,855.0 267 60.00 4.645 0.212 3.9 06/23/09 40,226,679.9 279.8 1,840.02,885.8 268 60.00 4.610 0.213 3.6 06/23/09 39,926,945.6 279.4 1,840.02,864.3 268 60.00 3.392 0.155 3.9 06/23/09 40,587,836.0 280.2 1,840.02,889.7 268 60.00 3.155 0.146 3.9 06/23/09 40,644,822.9 280.2 1,840.02,893.7 268 60.00 3.418 0.158 3.9 06/23/09 40,131,258.7 280.2 1,840.02,879.0 268 60.00 3.392 0.156 4.3 06/23/09 40,362,689.3 280.9 1,840.02,895.6 268 60.00 3.392 0.157 4.6 06/23/09 40,239,011.4 280.9 1,840.02,886.7 266 60.00 3.740 0.173 4.4 06/23/09 40,698,728.6 280.51,840.02,875.5 264 60.00 4.063 0.187 4.0 06/23/09 39,856,639.1 278.1 1,840.02,816.0 257 60.00 3.886 0.175 3.3 06/23/09 37,498,489.3 275.2 1,840.02,628.9 238 60.00 3.560 0.150 3.6 06/23/09 36,841,535.2 274.51,840.02,542.9 229 60.00 2.983 0.121 3.1 06/23/09 32,148,306.4 268.7 1,840.02,253.9 200 60.00 3.204 0.115 2.9 06/23/09 28,129,366.2 266.6 1,840.0 1,941.5 172 60.00 2.803 0.087 3.3 06/23/09 27,345,799.1 267.9 1,840.0 1,887.5 166 60.00 2.622 0.079 3.9 06/23/09 27,733,363.1 272.4 1,840.0 1,899.1 175 60.00 3.007 0.091 4.1 06/22/09 37,347,798.7 278.1 1,840.02,618.4 243 60.00 3.471 0.145 4.3 06/22/09 39,193,280.6 278.2 1,840.02,811.7 261 60.00 3.566 0.160 4.7 06/22/09 39,260,554.1 279.9 1,840.02,816.6 262 60.00 3.740 0.168 4.3 06/22/09 40,140,069.3 280.51,840.02,879.6 268 60.00 4.088 0.188 4.1 06/22/09 40,201,017.3 281.1 1,840.02,905.8 268 60.00 3.712 0.172 3.7 06/22/09 40,241,422.6 281.7 1,840.02,908.7 268 60.00 3.539 0.165 3.2 06/22/09 39,859,823.9 281.1 1,840.02,924.5 270 60.00 3.147 0.147 06/22/09 39,392,854.2 281.1 1,840.02,954.5 271 60.00 2.662 0.126

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 5.3 5.3 06/25/09 41,058,935.4 279.6 1,840.02,878.6 268 60.00 4.717 0.217 5.3 06/25/09 40,768,672.9 279.1 1,840.02,836.1 267 60.00 4.754 0.216 5.4 06/25/09 41,115,010.7 279.4 1,840.02,860.2 268 60.00 4.754 0.217 5.7 06/25/09 41,083,213.7 279.1 1,840.02,857.9 268 60.00 4.844 0.221 5.7 06/25/09 40,763,479.7 278.4 1,840.02,857.8 268 60.00 5.073 0.232 5.9 06/25/09 39,734,172.0 277.2 1,840.02,785.7 263 60.00 5.073 0.226 5.9 06/25/09 39,233,852.1 277.6 1,840.02,729.3 256 60.00 5.292 0.231 5.6 06/25/09 39,940,579.4 278.4 1,840.02,800.2 262 60.00 5.251 0.235 6.0 06/25/09 39,630,728.9 276.7 1,840.02,778.5 260 60.00 4.984 0.221 6.2 06/25/09 40,552,979.3 277.8 1,840.02,843.1 267 60.00 5.340 0.243 5.8 06/25/09 40,935,687.1 277.2 1,840.02,847.7 268 60.00 5.561 0.253 5.1 06/25/09 38,698,210.5 274.6 1,840.02,671.0 248 60.00 5.244 0.224 4.8 06/25/09 33,866,728.2 268.6 1,840.02,429.6 215 60.00 4.436 0.172 4.7 06/25/09 28,190,867.1 268.1 1,840.0 1,930.5 175 60.00 4.374 0.135 4.6 06/25/09 28,110,046.8 268.3 1,840.0 1,924.9 173 60.00 4.283 0.132 5.0 06/25/09 26,314,079.0 269.3 1,840.0 1,787.6 157 60.00 4.225 0.121 5.9 06/25/09 28,906,382.0 271.0 1,840.0 1,995.1 181 60.00 4.520 0.144 6.7 06/25/09 33,472,521.9 276.7 1,840.02,346.7 218 60.00 5.251 0.197 6.8 06/24/09 38,500,155.6 280.6 1,840.02,782.9 258 60.00 5.784 0.257 6.4 06/24/09 40,474,930.7 280.51,840.02,903.6 269 60.00 5.915 0.275 6.2 06/24/09 39,757,308.2 279.0 1,840.02,873.7 265 60.00 5.525 0.254 6.3 06/24/09 39,256,773.6 279.1 1,840.02,837.6 261 60.00 5.352 0.243 6.3 06/24/09 39,019,490.1 279.6 1,840.02,735.6 255 60.00 5.607 0.245 5.9 06/24/09 41,268,566.1 280.6 1,840.02,893.3 270 60.00 5.607 0.259 5.8 06/24/09 39,830,212.1 279.3 1,840.02,857.4 267 60.00 5.132 0.234 6.0 06/24/09 39,103,120.1 280.2 1,840.02,869.0 267 60.00 4.933 0.226 6.4 06/24/09 39,622,108.9 280.51,840.02,907.0 270 60.00 5.103 0.237 5.9 06/24/09 40,511,378.3 280.6 1,840.02,906.2 269 60.00 5.567 0.259 6.0 06/24/09 39,440,351.3 278.6 1,840.02,765.1 257 60.00 5.251 0.232 5.7 06/24/09 39,954,549.5 280.1 1,840.02,801.2 261 60.00 5.340 0.239 6.0 06/24/09 39,989,093.4 280.2 1,840.02,890.5 269 60.00 4.921 0.227 6.1 06/24/09 40,096,706.5 280.2 1,840.02,898.3 271 60.00 5.180 0.240 5.8 06/24/09 40,063,553.9 279.3 1,840.02,939.5 273 60.00 5.188 0.244 6.1 06/24/09 40,432,962.0 280.2 1,840.02,944.6 273 60.00 4.970 0.234 6.0 06/24/09 40,064,108.0 279.4 1,840.02,917.7 267 60.00 5.227 0.244 5.6 06/24/09 37,604,855.2 276.8 1,840.02,697.8 245 60.00 5.219 0.225 06/24/09 34,221,578.0 272.4 1,840.02,417.9 218 60.00 4.946 0.191

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 2.8 2.3 06/27/09 31,630,483.6 267.8 1,840.02,269.1 200 60.00 2.435 0.088 2.8 06/27/09 27,229,043.6 263.9 1,840.0 1,968.2 169 60.00 1.986 0.062 2.6 06/27/09 24,247,201.9 264.51,840.0 1,726.3 151 60.00 2.454 0.068 2.7 06/27/09 24,602,055.2 265.4 1,840.0 1,738.2 151 60.00 2.296 0.064 2.6 06/27/09 25,026,541.4 265.8 1,840.0 1,741.0 155 60.00 2.422 0.067 2.7 06/27/09 25,399,925.7 267.51,840.0 1,767.0 157 60.00 2.332 0.066 3.0 06/27/09 28,488,012.9 271.6 1,840.02,043.7 180 60.00 2.349 0.077 3.5 06/26/09 33,493,961.1 274.3 1,840.02,439.2 213 60.00 2.571 0.100 3.8 06/26/09 33,545,778.3 275.6 1,840.02,406.6 217 60.00 3.044 0.117 4.0 06/26/09 37,812,415.8 278.9 1,840.02,774.3 254 60.00 3.232 0.143 4.3 06/26/09 39,547,371.0 280.3 1,840.02,901.5 264 60.00 3.402 0.158 4.5 06/26/09 38,104,730.9 278.51,840.02,795.7 252 60.00 3.657 0.163 4.8 06/26/09 39,609,343.4 280.4 1,840.02,863.0 262 60.00 3.885 0.178 5.0 06/26/09 40,755,927.2 281.1 1,840.02,990.3 272 60.00 4.082 0.195 4.8 06/26/09 40,864,920.2 281.0 1,840.02,976.0 272 60.00 4.284 0.204 4.8 06/26/09 41,341,711.5 280.9 1,840.02,988.3 271 60.00 4.144 0.198 5.0 06/26/09 41,299,392.3 280.3 1,840.02,985.2 273 60.00 4.144 0.198 5.1 06/26/09 40,944,082.1 279.9 1,840.02,981.8 274 60.00 4.284 0.204 5.0 06/26/09 41,212,979.3 279.9 1,840.02,956.6 274 60.00 4.436 0.210 5.1 06/26/09 41,032,861.7 279.51,840.02,943.7 273 60.00 4.349 0.205 5.3 06/26/09 40,930,782.8 280.0 1,840.02,958.6 273 60.00 4.403 0.208 5.2 06/26/09 41,118,413.2 280.2 1,840.02,972.1 273 60.00 4.575 0.217 5.0 06/26/09 41,503,914.9 280.9 1,840.02,977.5 272 60.00 4.523 0.215 4.9 06/26/09 40,705,728.3 278.9 1,840.02,986.6 270 60.00 4.252 0.203 4.3 06/26/09 38,558,622.2 276.8 1,840.02,808.1 252 60.00 4.198 0.189 4.0 06/26/09 35,794,988.7 271.3 1,840.02,606.8 229 60.00 3.684 0.154 3.7 06/26/09 28,034,248.0 267.6 1,840.0 1,965.4 177 60.00 3.560 0.112 4.0 06/26/09 30,772,694.2 269.9 1,840.02,157.5 197 60.00 3.293 0.114 4.5 06/26/09 30,112,826.2 272.6 1,840.02,143.9 196 60.00 3.506 0.120 4.5 06/26/09 35,486,889.3 276.4 1,840.02,565.1 231 60.00 3.885 0.159 5.1 06/26/09 39,102,184.3 278.8 1,840.02,783.9 257 60.00 3.944 0.176 5.5 06/25/09 40,076,581.6 279.51,840.02,831.5 263 60.00 4.504 0.204 5.6 06/25/09 40,802,499.5 280.51,840.02,904.9 267 60.00 4.821 0.224 5.6 06/25/09 40,510,846.6 279.6 1,840.02,884.2 266 60.00 4.908 0.226 5.5 06/25/09 40,727,705.5 278.7 1,840.02,855.4 268 60.00 4.984 0.228 5.5 06/25/09 40,882,986.1 279.3 1,840.02,844.0 268 60.00 4.933 0.224 06/25/09 40,811,578.1 279.8 1,840.02,861.3 268 60.00 4.895 0.224

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 0.0 0.0 06/28/09 9,151,731.2 141.4 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 9,056,907.8 141.9 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 8,980,747.9 137.2 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 9,730,914.6 131.1 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 12,940,250.3 130.0 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 12,947,350.4 130.9 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 12,943,932.2 134.8 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 12,979,207.6 139.4 1,840.0 7.1 0 0.00 0.000 0.000 0.0 06/28/09 13,009,771.8 145.0 1,840.0 7.1 0 0.00 0.000 0.000 0.0 06/28/09 13,011,185.3 152.0 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 13,055,147.0 160.51,840.0 0.0 0 0.00 0.000 0.0 06/28/09 13,109,288.0 166.8 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 13,123,761.6 171.2 1,840.0 0.0 0 0.00 0.000 0.1 06/28/09 10,072,424.9 173.8 1,840.0 5.5 0 0.00 0.000 0.000 1.4 06/28/09 12,586,030.5 176.4 1,840.0 6.8 0 0.00 11.482 0.000 0.0 06/28/09 16,353,739.2 181.2 1,840.0 8.9 0 0.00160.742 0.000 0.0 06/28/09 16,318,768.8 188.9 1,840.0 8.9 0 0.00 0.000 0.000 0.0 06/28/09 17,730,945.3 202.2 1,840.0 260.2 0 0.00 0.000 0.000 0.1 06/28/09 17,619,245.3 215.3 1,840.0 9.6 0 0.00 0.000 0.000 1.2 06/28/09 18,952,362.5 231.1 1,840.0 10.3 0 0.00 11.482 0.000 2.5 06/27/09 23,530,183.4 251.7 1,840.0 434.8 22 50.00 4.052 0.023 3.0 06/27/09 23,441,119.8 265.6 1,840.0 1,439.6 123 60.00 2.540 0.058 4.5 06/27/09 25,162,466.4 270.51,840.0 1,791.4 159 60.00 2.629 0.075 4.5 06/27/09 32,646,653.4 276.9 1,840.02,253.4 213 60.00 4.068 0.147 3.7 06/27/09 40,224,231.2 280.1 1,840.02,841.9 267 60.00 3.974 0.181 2.7 06/27/09 39,229,892.4 277.7 1,840.02,750.4 257 60.00 3.293 0.145 2.5 06/27/09 38,409,305.0 278.1 1,840.02,651.1 251 60.00 2.441 0.103 2.5 06/27/09 40,286,368.8 278.8 1,840.02,868.2 268 60.00 2.191 0.100 3.4 06/27/09 40,725,472.8 279.7 1,840.02,899.4 268 60.00 2.191 0.102 3.8 06/27/09 40,834,942.8 279.6 1,840.02,862.9 268 60.00 3.026 0.139 3.5 06/27/09 40,771,218.7 279.1 1,840.02,858.4 268 60.00 3.382 0.155 3.5 06/27/09 40,660,074.8 278.7 1,840.02,872.7 268 60.00 3.091 0.142 4.0 06/27/09 40,854,725.7 279.3 1,840.02,886.5 268 60.00 3.091 0.143 3.9 06/27/09 40,832,693.1 278.7 1,840.02,884.9 268 60.00 3.533 0.163 3.8 06/27/09 40,216,008.3 276.51,840.02,797.6 260 60.00 3.498 0.156 3.1 06/27/09 37,797,460.9 274.6 1,840.02,752.6 251 60.00 3.256 0.143 06/27/09 34,601,231.3 270.4 1,840.02,538.7 222 60.00 2.637 0.107

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 0.0 0.0 06/30/09 10,258,583.5 80.51,840.0 0.0 0 0.00 0.000 0.0 06/30/09 9,281,019.5 80.8 1,840.0 0.0 0 0.00 0.000 0.1 06/30/09 9,365,483.1 81.4 1,840.0 0.0 0 0.00 0.000 2.3 06/30/09 9,446,843.3 82.1 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 9,581,859.8 82.8 1,840.0 0.0 0 0.00 0.000 2.8 06/30/09 9,519,890.3 83.4 1,840.0 0.0 0 0.00 0.000 0.7 06/30/09 13,114,032.2 84.1 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 9,310,594.5 84.6 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 9,330,377.2 85.2 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,332,384.9 85.8 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,376,229.9 86.2 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,583,104.9 86.8 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,754,077.4 87.51,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,342,152.2 88.3 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,917,589.9 88.9 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,992,104.5 89.9 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,918,389.1 90.3 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,801,474.2 90.6 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,752,215.7 91.3 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,700,130.4 92.2 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,360,111.8 93.6 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,045,444.5 94.9 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 10,015,126.5 96.3 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,928,370.4 97.9 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,430,653.3 99.7 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 8,704,505.3 101.51,840.0 0.0 0 0.00 0.000 0.1 06/29/09 8,843,041.9 103.51,840.0 0.0 0 0.00 0.000 2.3 06/29/09 8,863,586.5 105.9 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 8,976,948.8 108.9 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,051,175.2 111.9 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 12,912,403.3 115.4 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,178,793.4 119.0 1,840.0 0.0 0 0.00 0.000 0.0 06/29/09 9,446,738.9 122.9 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 9,511,200.9 126.9 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 9,492,190.1 130.7 1,840.0 0.0 0 0.00 0.000 0.0 06/28/09 9,489,713.0 134.4 1,840.0 0.0 0 0.00 0.000 06/28/09 9,221,374.2 138.3 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F FC 12:00 F F F F F F F F FC 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 0.0 0.0 07/01/09 8,755,972.1 77.2 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 8,847,996.7 77.2 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,307,967.2 77.1 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 10,071,858.2 77.0 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,584,904.3 76.8 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,201,483.7 76.8 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,088,690.7 76.4 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,090,346.9 76.1 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,236,883.3 75.9 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,176,012.0 75.7 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,237,939.2 75.7 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,224,145.0 75.51,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,320,999.5 75.51,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,458,174.2 75.51,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,499,328.0 75.7 1,840.0 0.0 0 0.00 0.000 0.1 07/01/09 9,527,516.2 76.0 1,840.0 0.0 0 0.00 0.000 2.3 07/01/09 9,518,147.9 76.4 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,518,329.0 76.8 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,483,558.6 77.3 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 13,169,007.8 78.1 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,578,058.7 78.8 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 9,592,158.4 79.4 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 9,531,876.6 79.9 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 9,719,051.7 80.2 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,552,559.7 80.2 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,521,091.7 80.0 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,474,898.7 80.0 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,376,664.7 80.0 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,293,700.0 80.1 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,519,376.9 80.1 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,652,576.8 80.1 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,585,598.3 80.4 1,840.0 0.0 0 0.00 0.000 1.3 06/30/09 10,472,406.1 80.4 1,840.0 0.0 0 0.00 0.000 2.1 06/30/09 10,469,936.4 80.2 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,519,853.5 80.1 1,840.0 0.0 0 0.00 0.000 0.0 06/30/09 10,520,125.7 80.1 1,840.0 0.0 0 0.00 0.000 06/30/09 10,677,919.0 80.3 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F FC 08:00 F F F F F F F F FC 09:00 F F F F F F F F FC 10:00 F F F F F F F F FC 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 0.0 0.0 07/03/09 2,400,213.4 82.3 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 7,516,615.2 78.4 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 8,754,651.2 78.4 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 8,810,708.1 78.3 1,840.0 0.0 0 0.00 0.000 0.1 07/03/09 8,890,084.8 78.4 1,840.0 0.0 0 0.00 0.000 2.3 07/03/09 8,905,380.7 78.51,840.0 0.0 0 0.00 0.000 0.0 07/03/09 8,950,979.5 78.6 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 8,971,921.1 78.8 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 12,883,226.3 79.2 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 8,855,844.2 79.7 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 8,970,499.1 80.4 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 9,010,759.2 80.9 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 9,206,633.1 81.1 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 9,496,251.4 81.0 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,328,831.1 80.8 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,333,332.2 80.6 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,343,402.3 80.3 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,390,838.7 80.1 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,331,901.4 79.7 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,228,843.0 79.2 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,306,841.7 78.7 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,340,929.1 78.2 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,326,526.0 77.7 1,840.0 0.0 0 0.00 0.000 0.1 07/02/09 10,386,940.9 77.2 1,840.0 0.0 0 0.00 0.000 2.3 07/02/09 10,302,460.6 76.9 1,840.0 0.0 0 0.00 0.000 1.8 07/02/09 10,315,065.3 76.4 1,840.0 0.0 0 0.00 0.000 0.5 07/02/09 10,379,382.8 76.2 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 10,281,799.4 75.9 1,840.0 0.0 0 0.00 0.000 0.1 07/02/09 9,673,784.7 75.8 1,840.0 0.0 0 0.00 0.000 2.3 07/02/09 8,944,048.5 75.9 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 8,860,788.3 76.0 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 8,886,225.4 76.3 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 12,799,773.3 76.4 1,840.0 0.0 0 0.00 0.000 0.0 07/02/09 8,960,444.9 76.51,840.0 0.0 0 0.00 0.000 0.0 07/02/09 8,909,409.5 76.7 1,840.0 0.0 0 0.00 0.000 0.0 07/01/09 8,906,076.3 77.0 1,840.0 0.0 0 0.00 0.000 07/01/09 8,655,329.1 77.2 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 0.0 0.0 07/04/09 668,988.0 119.51,840.0 0.0 0 0.00 0.000 0.0 07/04/09 655,164.7 120.2 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 603,456.6 120.9 1,840.0 0.0 0 0.00 0.000 0.1 07/04/09 484,896.1 121.6 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 509,938.5 121.8 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 540,830.8 120.2 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 524,106.4 117.9 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 584,432.3 115.1 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 604,342.0 112.4 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 598,086.8 112.3 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 559,556.0 112.2 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 589,737.3 112.3 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 564,226.6 112.3 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 559,752.8 112.3 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 568,961.8 112.6 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 647,199.6 112.4 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 638,644.5 112.4 1,840.0 0.0 0 0.00 0.000 0.1 07/04/09 596,235.9 112.4 1,840.0 0.0 0 0.00 0.000 2.4 07/04/09 624,076.6 112.51,840.0 0.0 0 0.00 0.000 0.0 07/04/09 564,466.7 112.6 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 573,103.2 112.8 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 7,226,312.1 112.8 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 472,162.4 112.6 1,840.0 0.0 0 0.00 0.000 0.0 07/04/09 554,076.3 112.51,840.0 0.0 0 0.00 0.000 0.0 07/03/09 436,691.7 112.3 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 510,285.4 112.1 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 525,152.8 111.9 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 523,602.2 111.8 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 523,433.9 111.7 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 536,237.8 111.6 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 477,022.7 111.4 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 479,008.1 110.9 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 543,498.8 110.51,840.0 0.0 0 0.00 0.000 0.0 07/03/09 464,200.3 109.2 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 482,212.0 108.2 1,840.0 0.0 0 0.00 0.000 0.0 07/03/09 495,722.3 106.4 1,840.0 0.0 0 0.00 0.000 07/03/09 457,490.0 100.0 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 11:00 12:00 C 0.3 0.3 07/06/09 22,339,889.1 150.6 1,840.0 218.5 0 60.00 1.914 0.007 0.3 07/06/09 23,136,961.3 121.1 1,840.0 188.6 0 60.00 2.296 0.007 0.1 07/06/09 21,596,859.1 103.0 1,840.0 164.3 0 45.00 2.460 0.005 0.1 07/06/09 6,509,773.6 122.0 1,840.0 3.5 0 0.00 11.482 0.000 0.0 07/06/09 446,117.9 127.7 1,840.0 0.0 0 0.00 0.000 0.0 07/06/09 469,219.7 125.2 1,840.0 0.0 0 0.00 0.000 0.1 07/06/09 453,804.4 122.3 1,840.0 0.0 0 0.00 0.000 2.4 07/06/09 510,976.0 120.3 1,840.0 0.0 0 0.00 0.000 0.0 07/06/09 459,517.1 120.9 1,840.0 0.0 0 0.00 0.000 0.0 07/06/09 473,196.7 122.3 1,840.0 0.0 0 0.00 0.000 0.0 07/06/09 7,161,827.5 124.1 1,840.0 0.0 0 0.00 0.000 0.1 07/06/09 459,846.6 125.51,840.0 0.0 0 0.00 0.000 0.1 07/06/09 496,538.1 127.9 1,840.0 0.0 0 0.00 0.000 0.1 07/05/09 464,850.5 129.7 1,840.0 0.0 0 0.00 0.000 0.1 07/05/09 407,713.1 131.3 1,840.0 0.0 0 0.00 0.000 0.1 07/05/09 403,663.0 131.9 1,840.0 0.0 0 0.00 0.000 0.1 07/05/09 376,500.7 130.4 1,840.0 0.0 0 0.00 0.000 0.1 07/05/09 428,616.2 128.6 1,840.0 0.0 0 0.00 0.000 0.1 07/05/09 360,356.1 126.3 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 390,386.7 123.51,840.0 0.0 0 0.00 0.000 0.0 07/05/09 445,086.7 120.2 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 445,911.9 119.0 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 411,296.5 118.6 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 486,176.9 118.1 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 512,744.6 117.7 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 510,743.9 117.4 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 500,796.3 117.3 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 574,445.1 116.7 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 548,596.2 116.2 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 518,927.9 115.6 1,840.0 0.0 0 0.00 0.000 0.1 07/05/09 587,969.8 114.9 1,840.0 0.0 0 0.00 0.000 2.3 07/05/09 629,390.3 114.9 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 610,420.2 115.4 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 502,557.7 115.8 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 7,244,554.1 116.3 1,840.0 0.0 0 0.00 0.000 0.0 07/05/09 517,770.9 117.0 1,840.0 0.0 0 0.00 0.000 07/05/09 560,156.8 118.0 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 C 14:00 15:00 C 16:00 C 17:00 18:00 ST ST ST 19:00 ST ST ST 20:00 ST ST ST 21:00 ST ST ST 22:00 ST ST ST 23:00 ST ST ST 00:00 ST ST ST 01:00 ST ST ST 02:00 C ST ST ST 03:00 ST ST ST 04:00 ST ST STC 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 3.4 3.4 07/08/09 26,100,856.4 260.6 1,840.0 1,829.9 159 60.00 3.026 0.089 3.3 07/08/09 25,925,640.7 261.0 1,840.0 1,817.6 159 60.00 3.026 0.088 3.6 07/07/09 26,096,223.3 265.3 1,840.0 1,829.6 169 60.00 2.937 0.086 4.8 07/07/09 30,418,437.3 271.6 1,840.02,215.2 207 60.00 3.085 0.109 4.9 07/07/09 36,944,758.8 276.51,840.02,690.6 252 60.00 4.113 0.177 4.6 07/07/09 39,435,741.2 277.2 1,840.02,893.4 271 60.00 4.167 0.193 3.8 07/07/09 41,738,803.9 276.6 1,840.03,017.0 286 60.00 3.971 0.192 3.5 07/07/09 40,559,111.7 275.0 1,840.02,953.8 280 60.00 3.256 0.154 3.5 07/07/09 40,792,280.2 274.9 1,840.02,970.7 282 60.00 2.999 0.142 3.8 07/07/09 41,514,655.5 275.9 1,840.03,045.9 289 60.00 2.977 0.145 3.9 07/07/09 40,962,249.5 274.9 1,840.02,960.8 280 60.00 3.280 0.155 3.8 07/07/09 43,109,460.3 275.6 1,840.03,092.6 291 60.00 3.392 0.168 3.9 07/07/09 41,553,635.4 273.1 1,840.03,003.6 279 60.00 3.280 0.158 4.0 07/07/09 35,028,783.5 266.51,840.02,474.9 225 60.00 3.444 0.136 3.9 07/07/09 35,094,847.8 266.51,840.02,365.1 220 60.00 3.704 0.140 3.7 07/07/09 35,700,497.6 265.3 1,840.02,464.1 228 60.00 3.526 0.139 3.8 07/07/09 32,841,283.6 262.4 1,840.02,248.9 206 60.00 3.372 0.121 3.6 07/07/09 30,555,583.5 260.4 1,840.02,092.4 192 60.00 3.463 0.116 2.2 07/07/09 29,518,567.9 257.2 1,840.0 1,989.3 184 60.00 3.333 0.106 2.9 07/07/09 27,054,640.2 254.4 1,840.0 1,882.1 169 60.00 1.973 0.059 5.6 07/07/09 23,885,881.0 246.0 1,840.0 1,583.7 141 60.00 2.729 0.069 5.6 07/07/09 24,041,030.2 235.1 1,840.0 1,136.7 96 60.00 7.390 0.134 5.6 07/07/09 24,210,795.1 231.4 1,840.0 644.7 44 60.00 13.122 0.135 5.6 07/07/09 25,845,692.7 226.8 1,840.0 561.9 25 60.00 16.074 0.144 5.6 07/07/09 25,310,281.0 224.7 1,840.0 467.7 19 60.00 18.911 0.141 5.6 07/07/09 24,992,082.5 223.7 1,840.0 230.9 2 60.00 37.822 0.140 5.6 07/06/09 25,016,360.4 224.1 1,840.0 149.6 0 60.00 58.452 0.140 5.6 07/06/09 25,189,237.7 222.3 1,840.0 205.3 0 60.00 42.865 0.141 5.6 07/06/09 25,283,853.4 219.3 1,840.0 192.4 0 60.00 45.926 0.141 5.6 07/06/09 24,831,166.6 220.7 1,840.0 108.0 0 54.00 80.371 0.125 5.6 07/06/09 25,091,217.4 219.9 1,840.0 122.7 0 60.00 71.441 0.140 0.1 07/06/09 25,294,039.8 217.6 1,840.0 82.5 0 60.00107.162 0.141 0.2 07/06/09 25,383,012.5 213.8 1,840.0 82.8 0 60.00 1.914 0.003 0.2 07/06/09 26,656,197.4 217.2 1,840.0 72.4 0 60.00 4.593 0.005 0.2 07/06/09 26,605,511.7 213.51,840.0 115.7 0 60.00 2.870 0.005 0.5 07/06/09 26,454,248.1 206.1 1,840.0 115.0 0 60.00 2.870 0.005 07/06/09 24,405,945.1 180.7 1,840.0 252.0 0 50.00 3.021 0.010

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 M 12:00 M 13:00 14:00 7.6 7.4 07/09/09 42,362,812.0 289.1 1,840.02,993.0 280 60.00 6.712 0.321 7.4 07/09/09 42,593,090.8 290.0 1,840.03,055.6 282 60.00 6.437 0.314 7.3 07/09/09 42,477,704.9 288.8 1,840.03,093.5 289 60.00 6.341 0.314 7.3 07/09/09 41,735,156.5 285.0 1,840.02,948.7 277 60.00 6.447 0.304 7.2 07/09/09 40,202,032.7 282.9 1,840.02,796.7 264 60.00 6.548 0.293 7.3 07/09/09 41,913,069.4 285.3 1,840.02,915.7 272 60.00 6.458 0.301 6.9 07/09/09 40,286,728.8 282.4 1,840.02,758.8 256 60.00 6.652 0.293 6.3 07/09/09 37,592,572.8 277.9 1,840.02,594.7 238 60.00 6.238 0.259 6.3 07/09/09 31,575,651.0 271.51,840.02,162.3 199 60.00 5.741 0.198 5.9 07/09/09 28,266,329.0 268.2 1,840.0 1,951.0 177 60.00 5.696 0.178 6.1 07/09/09 27,385,047.4 268.3 1,840.0 1,875.3 168 60.00 5.376 0.161 6.1 07/09/09 26,352,549.8 267.2 1,840.0 1,790.3 160 60.00 5.603 0.160 6.1 07/09/09 26,546,008.8 267.1 1,840.0 1,789.0 159 60.00 5.648 0.162 6.1 07/09/09 25,938,006.6 266.2 1,840.0 1,776.2 158 60.00 5.559 0.158 6.1 07/09/09 25,755,319.2 266.7 1,840.0 1,763.7 159 60.00 5.559 0.157 5.9 07/08/09 26,293,219.1 267.3 1,840.0 1,786.2 160 60.00 5.603 0.160 6.2 07/08/09 26,140,050.1 268.3 1,840.0 1,747.4 160 60.00 5.507 0.154 6.1 07/08/09 28,509,866.3 272.1 1,840.0 1,921.3 183 60.00 5.741 0.176 5.4 07/08/09 32,064,350.4 273.51,840.02,195.7 205 60.00 5.559 0.195 5.6 07/08/09 29,979,830.2 271.3 1,840.02,069.3 187 60.00 4.882 0.162 5.7 07/08/09 32,224,922.2 276.1 1,840.02,224.2 210 60.00 5.063 0.180 5.2 07/08/09 37,981,090.9 282.4 1,840.02,704.1 255 60.00 4.996 0.216 5.1 07/08/09 40,180,164.9 283.51,840.02,882.5 273 60.00 4.523 0.208 5.1 07/08/09 40,568,516.8 282.9 1,840.02,910.4 275 60.00 4.436 0.206 5.4 07/08/09 40,698,813.6 284.2 1,840.02,897.6 275 60.00 4.470 0.207 5.6 07/08/09 41,413,812.8 284.4 1,840.02,971.0 280 60.00 4.697 0.223 5.7 07/08/09 41,987,152.7 285.4 1,840.03,012.1 287 60.00 4.871 0.235 5.6 07/08/09 42,505,727.6 283.1 1,840.03,049.3 288 60.00 4.958 0.242 5.8 07/08/09 42,017,451.5 284.3 1,840.02,968.6 280 60.00 4.946 0.235 5.5 07/08/09 41,218,873.2 282.6 1,840.02,934.6 273 60.00 5.083 0.239 5.1 07/08/09 40,088,774.6 277.9 1,840.02,832.4 263 60.00 4.858 0.220 4.7 07/08/09 37,708,201.8 273.51,840.02,664.2 244 60.00 4.504 0.192 4.3 07/08/09 33,454,714.2 264.9 1,840.02,345.5 213 60.00 4.183 0.157 4.0 07/08/09 29,169,963.6 261.6 1,840.0 1,918.2 179 60.00 4.080 0.125 3.8 07/08/09 26,958,356.9 260.3 1,840.0 1,904.6 168 60.00 3.533 0.108 3.5 07/08/09 26,614,036.9 260.4 1,840.0 1,880.3 167 60.00 3.356 0.101 07/08/09 26,158,462.6 260.8 1,840.0 1,848.1 160 60.00 3.091 0.091

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 7.1 6.8 07/11/09 28,277,331.1 272.4 1,840.0 1,951.7 179 60.00 6.419 0.200 6.9 07/11/09 25,866,834.3 270.3 1,840.0 1,757.3 161 60.00 6.246 0.176 7.3 07/11/09 27,961,123.8 274.51,840.0 1,899.5 176 60.00 6.338 0.193 7.6 07/11/09 32,876,962.1 279.3 1,840.02,197.8 206 60.00 6.814 0.239 7.5 07/10/09 38,249,616.6 280.9 1,840.02,556.9 240 60.00 7.094 0.290 7.6 07/10/09 37,490,254.5 281.2 1,840.02,506.1 237 60.00 7.001 0.281 7.6 07/10/09 38,045,319.9 283.3 1,840.02,563.9 243 60.00 7.037 0.289 7.4 07/10/09 41,760,394.4 287.4 1,840.02,882.3 274 60.00 6.871 0.317 7.6 07/10/09 42,238,233.7 285.9 1,840.02,915.3 276 60.00 6.690 0.312 7.8 07/10/09 41,491,668.9 287.51,840.02,863.8 272 60.00 6.871 0.315 7.7 07/10/09 42,173,349.2 289.3 1,840.02,956.7 279 60.00 6.942 0.328 8.1 07/10/09 41,980,470.4 290.51,840.02,920.3 277 60.00 6.907 0.323 8.1 07/10/09 42,038,323.1 292.4 1,840.02,947.2 279 60.00 7.209 0.340 8.0 07/10/09 41,905,387.7 290.4 1,840.02,960.7 279 60.00 7.154 0.339 8.1 07/10/09 42,485,868.4 291.6 1,840.02,978.6 282 60.00 7.120 0.339 8.0 07/10/09 42,300,672.8 291.4 1,840.02,965.7 281 60.00 7.209 0.342 7.9 07/10/09 42,492,108.2 290.8 1,840.02,979.1 282 60.00 7.120 0.339 7.3 07/10/09 41,235,870.8 287.51,840.02,913.4 274 60.00 6.977 0.325 7.4 07/10/09 40,936,434.5 285.2 1,840.02,870.0 271 60.00 6.497 0.298 7.5 07/10/09 39,829,565.8 283.6 1,840.02,749.1 257 60.00 6.690 0.294 7.5 07/10/09 37,799,469.5 281.0 1,840.02,567.9 240 60.00 6.889 0.283 7.3 07/10/09 36,408,913.8 277.2 1,840.02,453.7 229 60.00 6.945 0.272 6.7 07/10/09 32,956,538.7 274.1 1,840.02,238.9 210 60.00 6.705 0.240 6.4 07/10/09 31,997,307.6 271.3 1,840.02,017.2 194 60.00 6.632 0.214 6.1 07/10/09 28,661,606.7 269.3 1,840.0 1,853.7 168 60.00 6.175 0.183 5.7 07/10/09 25,869,453.1 268.7 1,840.0 1,743.3 155 60.00 5.648 0.157 5.7 07/10/09 25,508,767.2 268.4 1,840.0 1,719.1 152 60.00 5.278 0.145 5.4 07/10/09 25,792,943.2 269.7 1,840.0 1,794.3 159 60.00 5.113 0.147 6.3 07/09/09 25,843,452.2 275.51,840.0 1,811.8 168 60.00 4.806 0.139 6.7 07/09/09 32,354,007.5 280.0 1,840.02,285.9 214 60.00 5.564 0.203 7.4 07/09/09 38,610,863.5 287.51,840.02,644.0 252 60.00 6.105 0.258 7.4 07/09/09 40,804,054.1 291.6 1,840.02,838.5 270 60.00 6.638 0.301 7.6 07/09/09 40,558,360.0 292.4 1,840.02,843.5 269 60.00 6.586 0.299 7.6 07/09/09 42,058,025.5 295.8 1,840.02,925.8 278 60.00 6.817 0.319 7.7 07/09/09 42,361,280.0 294.7 1,840.02,946.9 280 60.00 6.817 0.321 7.8 07/09/09 42,367,096.8 292.6 1,840.02,970.3 281 60.00 6.853 0.326 07/09/09 42,311,848.5 289.51,840.02,989.4 280 60.00 6.889 0.329

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 6.7 6.8 07/12/09 40,105,078.9 284.3 1,840.02,768.1 262 60.00 6.057 0.268 6.6 07/12/09 41,422,020.5 285.4 1,840.02,881.5 272 60.00 6.100 0.281 6.2 07/12/09 42,153,494.8 284.51,840.02,955.3 276 60.00 5.874 0.278 6.2 07/12/09 40,376,380.3 283.7 1,840.02,852.7 264 60.00 5.476 0.250 6.3 07/12/09 39,332,112.7 283.0 1,840.02,757.5 258 60.00 5.518 0.243 6.2 07/12/09 38,987,012.0 281.51,840.02,754.5 257 60.00 5.564 0.245 6.3 07/12/09 37,838,487.1 281.1 1,840.02,714.5 253 60.00 5.393 0.234 6.3 07/12/09 37,019,853.6 279.1 1,840.02,595.4 240 60.00 5.607 0.233 6.1 07/12/09 36,149,601.1 278.3 1,840.02,534.4 232 60.00 5.607 0.227 5.9 07/12/09 33,584,096.8 274.3 1,840.02,281.5 210 60.00 5.603 0.204 5.4 07/12/09 29,847,237.6 270.2 1,840.02,060.1 186 60.00 5.334 0.176 5.3 07/12/09 26,534,077.5 268.3 1,840.0 1,831.4 160 60.00 4.882 0.143 4.9 07/12/09 25,523,428.1 268.1 1,840.0 1,733.9 152 60.00 4.868 0.135 4.8 07/12/09 25,096,833.9 268.1 1,840.0 1,732.2 151 60.00 4.430 0.123 5.1 07/12/09 24,348,488.0 268.6 1,840.0 1,707.0 151 60.00 4.272 0.117 5.1 07/12/09 24,750,146.0 269.0 1,840.0 1,735.2 152 60.00 4.539 0.126 5.5 07/12/09 25,539,140.9 272.4 1,840.0 1,707.2 160 60.00 4.761 0.130 5.5 07/11/09 31,058,350.9 275.2 1,840.02,093.0 197 60.00 5.093 0.170 5.9 07/11/09 31,123,358.6 275.3 1,840.02,097.4 196 60.00 5.093 0.171 6.3 07/11/09 33,058,835.2 279.3 1,840.02,281.8 213 60.00 5.334 0.195 6.5 07/11/09 37,785,615.5 285.3 1,840.02,690.2 251 60.00 5.522 0.238 6.5 07/11/09 38,534,644.8 284.4 1,840.02,722.6 255 60.00 5.741 0.250 6.8 07/11/09 37,996,505.2 285.7 1,840.02,684.6 251 60.00 5.741 0.246 6.8 07/11/09 40,986,291.7 288.2 1,840.02,828.9 268 60.00 6.148 0.278 7.0 07/11/09 39,521,571.4 288.2 1,840.02,835.3 267 60.00 5.915 0.268 7.1 07/11/09 40,712,696.3 290.2 1,840.02,898.6 274 60.00 6.135 0.284 7.2 07/11/09 41,160,988.4 289.51,840.02,908.1 275 60.00 6.271 0.292 7.0 07/11/09 40,433,958.3 287.7 1,840.02,900.7 271 60.00 6.263 0.290 7.0 07/11/09 39,633,417.6 287.51,840.02,864.8 265 60.00 6.043 0.277 7.2 07/11/09 37,950,902.2 285.8 1,840.02,722.6 249 60.00 6.089 0.265 7.8 07/11/09 38,371,479.4 286.51,840.02,731.8 253 60.00 6.310 0.276 8.0 07/11/09 38,556,717.6 286.0 1,840.02,766.0 255 60.00 6.785 0.300 7.7 07/11/09 38,202,845.1 282.9 1,840.02,740.7 253 60.00 6.959 0.305 7.2 07/11/09 36,816,293.6 278.9 1,840.02,561.1 234 60.00 6.907 0.283 7.0 07/11/09 31,237,786.8 274.1 1,840.02,156.1 194 60.00 6.509 0.224 6.8 07/11/09 27,752,381.9 270.51,840.0 1,900.4 167 60.00 6.379 0.194 07/11/09 25,904,725.7 271.51,840.0 1,745.8 158 60.00 6.296 0.176

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 4.9 5.7 07/14/09 26,691,327.3 267.3 1,840.0 1,769.7 163 60.00 4.611 0.130 5.4 07/14/09 26,020,952.9 267.8 1,840.0 1,711.2 157 60.00 5.409 0.148 5.3 07/14/09 25,774,342.9 267.3 1,840.0 1,722.9 154 60.00 5.041 0.139 5.3 07/14/09 25,207,240.3 267.3 1,840.0 1,671.3 151 60.00 4.988 0.133 5.3 07/14/09 25,733,220.4 267.6 1,840.0 1,720.2 153 60.00 4.947 0.136 5.3 07/14/09 25,742,432.8 267.7 1,840.0 1,706.8 153 60.00 4.988 0.136 5.2 07/13/09 25,632,876.6 269.4 1,840.0 1,727.4 156 60.00 4.907 0.136 5.8 07/13/09 26,425,128.3 273.0 1,840.0 1,809.5 165 60.00 4.738 0.137 5.6 07/13/09 33,898,613.0 279.0 1,840.02,302.9 218 60.00 5.327 0.196 5.8 07/13/09 38,986,717.4 282.8 1,840.02,691.0 255 60.00 5.063 0.218 5.5 07/13/09 37,112,330.0 280.4 1,840.02,521.2 239 60.00 5.327 0.215 5.9 07/13/09 39,581,020.9 285.3 1,840.02,731.9 260 60.00 4.972 0.217 6.3 07/13/09 42,022,533.2 288.4 1,840.02,900.5 275 60.00 5.334 0.247 4.7 07/13/09 41,574,293.6 287.2 1,840.02,869.5 276 60.00 5.696 0.261 5.8 07/13/09 42,208,339.7 287.51,840.02,936.2 279 60.00 4.216 0.198 6.7 07/13/09 42,803,195.5 288.51,840.02,977.6 281 60.00 5.203 0.248 6.6 07/13/09 42,771,431.1 287.0 1,840.02,952.1 280 60.00 6.057 0.286 6.7 07/13/09 42,733,577.5 287.2 1,840.02,903.1 277 60.00 6.062 0.281 6.6 07/13/09 42,517,019.0 286.3 1,840.02,911.5 277 60.00 6.105 0.284 6.6 07/13/09 42,066,256.6 284.9 1,840.02,903.5 274 60.00 5.967 0.277 6.3 07/13/09 41,544,894.0 283.7 1,840.02,890.1 267 60.00 5.920 0.274 6.5 07/13/09 36,995,748.2 280.3 1,840.02,613.8 238 60.00 5.564 0.233 6.5 07/13/09 37,905,941.9 281.3 1,840.02,739.9 246 60.00 5.611 0.246 5.8 07/13/09 35,737,696.4 274.3 1,840.02,563.8 229 60.00 5.654 0.232 5.4 07/13/09 29,093,070.6 268.7 1,840.02,023.9 179 60.00 5.203 0.168 5.5 07/13/09 25,687,914.3 267.7 1,840.0 1,787.0 155 60.00 4.844 0.138 5.1 07/13/09 25,976,629.3 267.1 1,840.0 1,793.0 157 60.00 4.972 0.143 5.3 07/13/09 24,926,120.3 267.51,840.0 1,720.4 151 60.00 4.611 0.127 5.3 07/13/09 25,306,305.7 267.8 1,840.0 1,760.4 153 60.00 4.754 0.134 5.3 07/13/09 25,202,851.9 267.9 1,840.0 1,739.6 151 60.00 4.792 0.133 5.1 07/12/09 25,759,611.4 267.8 1,840.0 1,778.0 156 60.00 4.792 0.136 6.0 07/12/09 25,967,014.3 273.0 1,840.0 1,792.3 167 60.00 4.611 0.132 6.5 07/12/09 33,531,798.9 280.2 1,840.02,369.1 222 60.00 5.299 0.201 6.1 07/12/09 37,817,770.0 282.3 1,840.02,713.0 252 60.00 5.654 0.245 6.4 07/12/09 34,951,865.7 278.2 1,840.02,488.4 229 60.00 5.346 0.213 6.6 07/12/09 35,785,524.8 280.0 1,840.02,528.4 237 60.00 5.652 0.229 07/12/09 39,004,107.7 282.7 1,840.02,692.1 254 60.00 5.967 0.257

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 S S SC 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 4.9 5.4 07/15/09 40,668,698.9 292.51,840.02,873.4 272 60.00 4.328 0.199 5.7 07/15/09 40,901,438.2 298.6 1,840.02,912.0 275 60.00 4.733 0.220 5.7 07/15/09 40,675,589.2 300.0 1,840.02,984.4 278 60.00 4.848 0.231 5.7 07/15/09 41,489,041.5 301.3 1,840.03,021.5 278 60.00 4.884 0.236 5.8 07/15/09 42,088,305.1 302.8 1,840.03,019.4 281 60.00 4.958 0.239 6.0 07/15/09 42,473,188.0 304.2 1,840.03,000.8 282 60.00 5.123 0.246 6.6 07/15/09 42,728,889.3 309.1 1,840.03,042.1 287 60.00 5.259 0.256 6.6 07/15/09 44,554,478.1 310.7 1,840.03,244.7 306 60.00 5.655 0.293 6.4 07/15/09 44,543,549.3 307.8 1,840.03,268.2 306 60.00 5.613 0.293 6.4 07/15/09 44,602,420.7 304.3 1,840.03,248.2 306 60.00 5.484 0.285 6.2 07/15/09 44,613,108.7 300.2 1,840.03,249.0 307 60.00 5.484 0.285 5.7 07/15/09 44,758,753.8 294.1 1,840.03,211.0 305 60.00 5.393 0.277 5.2 07/15/09 42,067,429.6 282.1 1,840.02,926.4 279 60.00 5.113 0.239 5.2 07/15/09 36,340,303.9 278.4 1,840.02,449.0 232 60.00 4.815 0.189 4.8 07/15/09 36,751,029.5 275.51,840.02,556.6 234 60.00 4.664 0.191 4.4 07/15/09 30,341,395.0 270.1 1,840.02,061.2 191 60.00 4.409 0.145 3.7 07/15/09 29,237,591.3 267.0 1,840.0 1,906.8 172 60.00 4.210 0.128 4.4 07/15/09 24,952,380.9 269.2 1,840.0 1,695.1 153 60.00 3.399 0.092 4.6 07/15/09 27,848,921.0 271.51,840.0 1,891.9 174 60.00 4.042 0.122 4.4 07/14/09 29,061,884.9 272.4 1,840.02,005.9 185 60.00 4.159 0.133 5.0 07/14/09 26,964,958.7 273.7 1,840.0 1,875.8 172 60.00 3.947 0.118 5.7 07/14/09 32,474,493.1 279.0 1,840.02,223.8 209 60.00 4.556 0.162 5.9 07/14/09 37,912,141.8 283.4 1,840.02,678.6 252 60.00 5.034 0.216 5.7 07/14/09 36,860,638.7 280.4 1,840.02,584.3 243 60.00 5.251 0.217 5.7 07/14/09 38,750,685.1 284.4 1,840.02,737.8 257 60.00 5.034 0.220 5.8 07/14/09 38,825,000.9 284.1 1,840.02,722.0 256 60.00 5.073 0.221 6.2 07/14/09 39,082,989.6 287.1 1,840.02,718.8 260 60.00 5.203 0.226 6.2 07/14/09 40,667,766.5 286.8 1,840.02,851.2 273 60.00 5.518 0.252 6.2 07/14/09 38,826,664.9 283.6 1,840.02,701.0 259 60.00 5.561 0.240 6.0 07/14/09 39,390,817.4 284.1 1,840.02,740.2 262 60.00 5.561 0.244 5.8 07/14/09 38,231,587.1 280.9 1,840.02,618.1 245 60.00 5.467 0.229 5.8 07/14/09 34,499,021.1 278.2 1,840.02,287.4 216 60.00 5.458 0.200 6.2 07/14/09 36,410,189.1 277.9 1,840.02,453.7 231 60.00 5.370 0.211 5.9 07/14/09 32,786,423.9 272.8 1,840.02,191.7 206 60.00 5.787 0.203 6.1 07/14/09 30,867,138.5 274.0 1,840.02,080.2 194 60.00 5.463 0.182 5.3 07/14/09 33,202,663.2 271.9 1,840.02,201.5 203 60.00 5.741 0.202 07/14/09 28,788,859.4 267.51,840.0 1,893.2 173 60.00 5.029 0.152

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 5.0 5.9 07/17/09 26,313,437.7 269.9 1,840.0 1,773.3 165 60.00 4.630 0.131 5.6 07/17/09 29,860,927.2 269.1 1,840.02,012.4 183 60.00 5.463 0.176 6.3 07/17/09 26,184,883.5 266.6 1,840.0 1,750.4 157 60.00 5.227 0.146 6.4 07/17/09 26,830,633.9 266.51,840.0 1,808.2 165 60.00 5.833 0.169 6.7 07/17/09 26,221,983.9 266.8 1,840.0 1,695.9 156 60.00 6.175 0.167 6.7 07/17/09 25,694,041.9 266.9 1,840.0 1,647.8 152 60.00 6.519 0.172 7.1 07/17/09 25,601,912.0 266.6 1,840.0 1,669.7 151 60.00 6.411 0.171 7.0 07/17/09 25,035,746.1 266.0 1,840.0 1,660.0 151 60.00 6.682 0.177 6.2 07/16/09 25,081,876.4 266.9 1,840.0 1,663.0 153 60.00 6.588 0.175 6.6 07/16/09 25,687,636.3 270.51,840.0 1,717.2 158 60.00 5.787 0.159 7.2 07/16/09 29,106,742.4 274.9 1,840.0 1,977.4 184 60.00 6.062 0.192 7.0 07/16/09 35,667,120.6 279.9 1,840.02,403.6 230 60.00 6.667 0.256 6.7 07/16/09 36,032,087.5 280.1 1,840.02,467.4 231 60.00 6.379 0.252 6.1 07/16/09 38,192,059.4 283.9 1,840.02,656.8 254 60.00 6.010 0.255 5.7 07/16/09 41,954,823.5 288.4 1,840.02,964.2 279 60.00 5.388 0.255 5.7 07/16/09 42,117,799.1 288.4 1,840.02,975.7 280 60.00 5.034 0.240 5.8 07/16/09 41,703,165.4 288.1 1,840.02,991.7 279 60.00 4.958 0.237 5.7 07/16/09 41,545,287.9 287.7 1,840.03,003.0 281 60.00 5.007 0.240 5.6 07/16/09 41,791,186.5 288.6 1,840.03,020.8 279 60.00 4.921 0.238 5.5 07/16/09 40,538,945.2 286.1 1,840.02,908.2 267 60.00 4.871 0.227 5.5 07/16/09 38,057,338.4 280.51,840.02,688.8 248 60.00 4.858 0.209 4.8 07/16/09 35,884,930.7 276.6 1,840.02,496.3 232 60.00 4.933 0.197 4.8 07/16/09 33,170,339.3 274.8 1,840.02,361.6 215 60.00 4.207 0.159 2.2 07/16/09 35,598,614.8 278.1 1,840.02,515.1 232 60.00 4.239 0.170 1.6 07/16/09 37,579,939.1 278.8 1,840.02,634.7 244 60.00 1.958 0.082 2.1 07/16/09 35,938,095.4 273.9 1,840.02,578.2 232 60.00 1.392 0.057 3.9 07/16/09 28,053,738.8 267.51,840.0 1,951.6 172 60.00 1.884 0.059 3.7 07/16/09 27,412,253.3 268.3 1,840.0 1,802.6 166 60.00 3.701 0.107 3.9 07/16/09 26,706,392.7 266.9 1,840.0 1,843.3 163 60.00 3.345 0.099 3.8 07/16/09 25,711,255.1 266.8 1,840.0 1,718.7 155 60.00 3.641 0.100 3.8 07/16/09 25,648,587.9 268.1 1,840.0 1,770.3 159 60.00 3.435 0.097 3.8 07/16/09 27,437,593.3 270.2 1,840.0 1,878.9 168 60.00 3.463 0.104 3.5 07/15/09 28,810,365.0 274.2 1,840.0 1,957.2 179 60.00 3.490 0.109 2.4 07/15/09 34,402,367.7 279.8 1,840.02,374.5 223 60.00 3.164 0.120 3.7 07/15/09 40,102,591.7 284.6 1,840.02,811.6 268 60.00 2.136 0.096 4.8 07/15/09 40,689,659.0 286.0 1,840.02,874.8 274 60.00 3.268 0.150 07/15/09 39,924,596.2 286.8 1,840.02,799.1 266 60.00 4.272 0.191

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 5.8 5.9 07/18/09 35,198,949.6 278.6 1,840.02,544.3 236 60.00 5.007 0.204 5.7 07/18/09 32,709,697.8 272.6 1,840.02,346.6 213 60.00 5.132 0.193 6.1 07/18/09 29,687,176.3 270.9 1,840.02,113.6 194 60.00 4.996 0.169 5.4 07/18/09 31,403,416.7 272.1 1,840.02,201.6 206 60.00 5.429 0.191 5.3 07/18/09 31,891,931.9 271.51,840.02,253.2 209 60.00 4.769 0.172 5.5 07/18/09 30,410,816.1 273.1 1,840.02,198.2 203 60.00 4.575 0.161 5.3 07/18/09 34,515,660.4 274.9 1,840.02,551.2 228 60.00 4.643 0.189 5.2 07/18/09 30,391,870.2 272.0 1,840.02,229.8 200 60.00 4.508 0.161 4.7 07/18/09 30,760,855.4 271.0 1,840.02,256.9 206 60.00 4.423 0.160 4.6 07/18/09 31,277,022.2 272.51,840.02,260.8 208 60.00 4.057 0.147 4.4 07/18/09 31,639,647.5 272.1 1,840.02,269.8 208 60.00 4.001 0.145 5.4 07/18/09 31,714,403.7 270.6 1,840.02,275.1 205 60.00 3.827 0.139 5.1 07/18/09 29,877,076.4 270.0 1,840.02,094.6 196 60.00 4.806 0.161 5.1 07/18/09 31,452,563.2 268.3 1,840.02,256.4 205 60.00 4.436 0.160 5.5 07/18/09 26,258,223.3 264.8 1,840.0 1,869.5 168 60.00 4.470 0.134 5.9 07/18/09 25,142,614.9 264.0 1,840.0 1,762.7 156 60.00 4.895 0.138 6.0 07/18/09 25,330,860.1 264.9 1,840.0 1,734.6 160 60.00 5.376 0.149 6.1 07/18/09 26,781,057.7 265.3 1,840.0 1,848.5 170 60.00 5.424 0.160 6.2 07/18/09 28,464,860.4 267.0 1,840.0 1,887.4 176 60.00 5.741 0.173 6.2 07/18/09 28,752,650.7 268.1 1,840.0 1,922.1 178 60.00 5.787 0.178 6.3 07/18/09 30,404,604.3 268.4 1,840.02,115.1 192 60.00 5.561 0.188 6.2 07/17/09 27,831,206.4 267.2 1,840.0 1,951.2 178 60.00 5.607 0.175 6.5 07/17/09 26,656,467.0 267.3 1,840.0 1,854.3 167 60.00 5.561 0.165 6.7 07/17/09 27,405,946.9 269.4 1,840.0 1,891.6 173 60.00 5.876 0.178 6.2 07/17/09 30,357,988.6 272.3 1,840.02,177.9 201 60.00 5.828 0.203 5.3 07/17/09 30,254,957.8 266.7 1,840.02,170.5 197 60.00 5.393 0.187 5.1 07/17/09 26,585,472.7 264.4 1,840.0 1,863.8 169 60.00 4.717 0.141 5.5 07/17/09 24,708,203.8 265.3 1,840.0 1,705.4 152 60.00 4.611 0.126 6.7 07/17/09 25,220,573.2 266.7 1,840.0 1,740.8 156 60.00 4.972 0.138 7.0 07/17/09 27,187,124.8 268.51,840.0 1,861.7 170 60.00 6.105 0.182 7.5 07/17/09 29,188,702.3 271.7 1,840.02,014.7 193 60.00 6.328 0.204 5.9 07/17/09 34,756,703.7 273.1 1,840.02,380.1 224 60.00 6.834 0.260 5.6 07/17/09 31,117,459.9 268.6 1,840.02,113.9 192 60.00 5.419 0.183 5.7 07/17/09 27,041,296.7 267.9 1,840.0 1,837.0 164 60.00 5.144 0.151 5.9 07/17/09 25,965,626.7 269.0 1,840.0 1,778.1 161 60.00 5.194 0.148 4.1 07/17/09 29,767,949.7 269.7 1,840.02,054.6 191 60.00 5.334 0.175 07/17/09 27,138,722.8 267.9 1,840.0 1,902.7 170 60.00 3.649 0.111

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 3.7 4.0 07/20/09 38,608,357.3 278.4 1,840.02,853.6 268 60.00 3.124 0.143 4.0 07/20/09 39,458,439.0 279.4 1,840.02,873.6 270 60.00 3.427 0.157 3.3 07/20/09 38,490,594.7 277.0 1,840.02,803.1 259 60.00 3.427 0.154 2.9 07/20/09 35,375,377.6 269.7 1,840.02,537.8 227 60.00 2.870 0.116 2.4 07/20/09 26,657,363.2 264.3 1,840.0 1,897.9 169 60.00 2.542 0.077 2.5 07/20/09 26,160,264.3 266.1 1,840.0 1,848.3 168 60.00 2.120 0.063 2.5 07/20/09 26,814,746.2 265.2 1,840.0 1,894.5 168 60.00 2.208 0.067 2.8 07/20/09 25,327,616.3 264.6 1,840.0 1,706.9 159 60.00 2.315 0.063 2.8 07/20/09 24,595,816.0 264.3 1,840.0 1,711.0 152 60.00 2.512 0.069 3.1 07/20/09 24,806,178.7 265.7 1,840.0 1,725.6 153 60.00 2.512 0.069 3.0 07/19/09 25,839,275.7 268.51,840.0 1,783.5 162 60.00 2.803 0.080 3.8 07/19/09 28,549,134.3 269.8 1,840.02,079.1 184 60.00 2.571 0.085 3.9 07/19/09 29,936,515.6 271.6 1,840.02,180.2 197 60.00 3.256 0.114 4.1 07/19/09 34,692,562.3 277.0 1,840.02,488.8 230 60.00 3.392 0.135 4.0 07/19/09 35,118,839.6 274.2 1,840.02,519.4 225 60.00 3.566 0.144 4.2 07/19/09 33,948,328.5 273.9 1,840.02,435.4 219 60.00 3.479 0.135 4.3 07/19/09 32,430,730.4 274.51,840.02,361.8 219 60.00 3.599 0.136 4.5 07/19/09 35,979,445.1 277.4 1,840.02,620.2 242 60.00 3.684 0.154 4.8 07/19/09 37,456,980.7 277.6 1,840.02,626.1 243 60.00 4.005 0.168 5.1 07/19/09 36,163,031.5 276.9 1,840.02,555.0 234 60.00 4.239 0.173 5.4 07/19/09 31,660,037.0 275.2 1,840.02,271.3 211 60.00 4.436 0.161 5.3 07/19/09 31,023,451.7 274.1 1,840.02,242.4 208 60.00 4.662 0.167 5.6 07/19/09 32,061,009.4 275.1 1,840.02,317.5 217 60.00 4.575 0.170 6.1 07/19/09 33,522,709.3 273.4 1,840.02,423.1 223 60.00 4.834 0.187 5.6 07/19/09 31,612,440.5 271.2 1,840.02,285.0 210 60.00 5.266 0.192 5.3 07/19/09 30,236,888.9 268.51,840.02,169.2 198 60.00 4.871 0.169 5.4 07/19/09 28,994,422.2 269.3 1,840.02,032.7 187 60.00 4.717 0.153 4.5 07/19/09 29,230,026.7 269.1 1,840.02,049.3 187 60.00 4.806 0.157 4.6 07/19/09 28,306,739.0 265.2 1,840.0 1,984.6 176 60.00 4.005 0.127 4.4 07/19/09 24,012,478.8 263.8 1,840.0 1,670.4 151 60.00 4.126 0.110 4.3 07/19/09 24,387,246.5 264.6 1,840.0 1,696.5 153 60.00 3.947 0.107 4.7 07/19/09 25,437,067.9 266.3 1,840.0 1,755.7 159 60.00 3.887 0.109 5.2 07/19/09 26,058,556.0 267.8 1,840.0 1,784.5 161 60.00 4.283 0.122 5.1 07/19/09 30,090,914.4 269.4 1,840.02,060.6 190 60.00 4.738 0.156 4.0 07/18/09 27,203,612.2 267.2 1,840.0 1,936.8 175 60.00 4.470 0.138 5.1 07/18/09 25,137,108.9 269.4 1,840.0 1,803.3 162 60.00 3.479 0.100 07/18/09 28,172,323.9 273.9 1,840.02,005.7 187 60.00 4.470 0.143

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 4.5 4.3 07/21/09 30,003,500.6 270.4 1,840.02,070.9 194 60.00 4.068 0.135 4.0 07/21/09 34,179,196.9 271.7 1,840.02,396.2 222 60.00 3.827 0.147 4.1 07/21/09 36,699,215.4 277.9 1,840.02,612.8 248 60.00 3.506 0.146 4.3 07/21/09 39,773,331.6 280.0 1,840.02,896.5 271 60.00 3.513 0.163 4.8 07/21/09 39,665,458.3 280.7 1,840.02,867.1 269 60.00 3.712 0.170 4.9 07/21/09 40,371,590.1 282.0 1,840.02,940.1 274 60.00 4.113 0.193 4.9 07/21/09 39,362,335.8 281.51,840.02,888.0 270 60.00 4.167 0.192 4.8 07/21/09 40,962,505.3 283.0 1,840.03,027.7 284 60.00 4.137 0.200 4.3 07/21/09 41,497,381.3 281.7 1,840.03,044.6 286 60.00 4.082 0.199 4.1 07/21/09 41,312,132.0 281.9 1,840.03,031.0 283 60.00 3.657 0.177 4.1 07/21/09 41,613,156.6 281.51,840.03,030.5 283 60.00 3.513 0.170 4.1 07/21/09 40,733,088.1 280.51,840.02,966.4 277 60.00 3.513 0.167 3.5 07/21/09 41,012,480.8 279.7 1,840.02,964.5 281 60.00 3.539 0.168 3.3 07/21/09 41,007,028.1 278.6 1,840.02,964.1 280 60.00 3.021 0.143 3.2 07/21/09 40,727,035.2 277.51,840.02,921.7 273 60.00 2.870 0.134 2.6 07/21/09 39,122,172.3 275.8 1,840.02,785.3 259 60.00 2.805 0.125 2.2 07/21/09 37,389,970.2 270.4 1,840.02,662.0 238 60.00 2.279 0.097 1.8 07/21/09 27,759,545.8 263.0 1,840.0 1,931.1 171 60.00 1.973 0.061 1.8 07/21/09 26,631,277.0 264.0 1,840.0 1,838.1 168 60.00 1.627 0.048 2.0 07/21/09 25,920,927.0 264.7 1,840.0 1,803.2 162 60.00 1.615 0.047 2.2 07/21/09 25,501,051.2 265.1 1,840.0 1,732.4 155 60.00 1.837 0.051 2.5 07/21/09 26,276,229.1 265.2 1,840.0 1,813.6 161 60.00 1.989 0.058 2.6 07/21/09 24,795,349.4 264.8 1,840.0 1,711.4 153 60.00 2.260 0.062 2.6 07/20/09 27,492,454.1 266.7 1,840.0 1,912.5 175 60.00 2.332 0.071 2.5 07/20/09 26,947,267.7 266.9 1,840.0 1,889.2 170 60.00 2.314 0.070 3.0 07/20/09 30,503,273.7 273.1 1,840.02,138.5 201 60.00 2.225 0.076 2.9 07/20/09 38,150,970.8 278.0 1,840.02,778.4 256 60.00 2.571 0.114 2.7 07/20/09 38,115,521.8 277.1 1,840.02,775.8 254 60.00 2.485 0.110 3.0 07/20/09 37,654,378.9 277.3 1,840.02,762.7 254 60.00 2.296 0.101 3.4 07/20/09 38,536,738.1 279.4 1,840.02,827.4 261 60.00 2.551 0.115 3.5 07/20/09 39,741,016.0 281.2 1,840.02,915.8 273 60.00 2.892 0.135 3.7 07/20/09 40,659,385.7 281.7 1,840.03,005.2 280 60.00 2.955 0.142 3.6 07/20/09 39,949,759.7 280.1 1,840.02,952.8 276 60.00 3.124 0.147 3.8 07/20/09 39,699,352.0 280.51,840.02,934.3 273 60.00 3.039 0.143 3.9 07/20/09 39,472,781.9 280.0 1,840.02,896.1 268 60.00 3.232 0.150 3.6 07/20/09 39,852,932.5 280.8 1,840.02,924.0 272 60.00 3.317 0.155 07/20/09 39,979,952.0 280.4 1,840.02,955.0 277 60.00 3.039 0.144

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 4.0 4.0 07/23/09 41,216,554.6 280.9 1,840.02,934.5 277 60.00 3.506 0.165 4.0 07/23/09 41,110,001.5 280.51,840.02,949.2 275 60.00 3.479 0.164 4.6 07/23/09 39,741,765.4 279.51,840.02,829.5 265 60.00 3.506 0.159 4.3 07/23/09 38,534,238.2 277.9 1,840.02,785.3 257 60.00 3.971 0.177 4.0 07/23/09 36,358,626.7 273.0 1,840.02,568.8 234 60.00 3.798 0.156 3.9 07/23/09 31,748,299.4 269.4 1,840.02,260.3 203 60.00 3.506 0.127 3.1 07/23/09 31,482,310.7 267.7 1,840.02,241.4 200 60.00 3.418 0.123 3.0 07/23/09 29,662,039.6 266.7 1,840.02,079.6 187 60.00 2.759 0.092 3.3 07/23/09 28,429,882.2 267.4 1,840.0 1,977.7 175 60.00 2.691 0.085 3.5 07/23/09 29,350,564.1 267.6 1,840.02,009.9 178 60.00 3.007 0.097 3.7 07/23/09 28,948,061.7 268.2 1,840.0 1,966.6 176 60.00 3.215 0.101 3.4 07/23/09 30,448,915.8 269.51,840.02,134.7 193 60.00 3.293 0.112 3.4 07/22/09 32,520,679.4 270.0 1,840.02,244.7 207 60.00 3.074 0.110 3.6 07/22/09 34,077,275.2 273.0 1,840.02,315.0 219 60.00 3.123 0.116 3.8 07/22/09 38,504,383.6 278.1 1,840.02,741.3 253 60.00 3.155 0.138 3.6 07/22/09 40,382,310.9 280.8 1,840.02,897.0 270 60.00 3.305 0.153 3.7 07/22/09 40,141,846.8 279.3 1,840.02,879.8 267 60.00 3.131 0.144 4.1 07/22/09 38,974,192.6 278.9 1,840.02,774.8 262 60.00 3.243 0.144 4.2 07/22/09 39,172,070.1 279.6 1,840.02,810.2 264 60.00 3.566 0.160 4.4 07/22/09 39,924,016.6 279.2 1,840.02,864.1 269 60.00 3.653 0.167 4.5 07/22/09 40,629,104.7 280.8 1,840.02,936.8 275 60.00 3.798 0.178 4.6 07/22/09 40,755,274.2 279.7 1,840.02,968.0 277 60.00 3.856 0.183 4.7 07/22/09 40,853,043.8 279.9 1,840.02,975.2 277 60.00 3.941 0.188 4.6 07/22/09 40,850,846.1 280.6 1,840.02,975.0 274 60.00 4.027 0.192 4.9 07/22/09 41,345,871.9 280.3 1,840.02,966.1 278 60.00 4.001 0.190 4.7 07/22/09 41,237,930.9 279.4 1,840.02,958.4 279 60.00 4.262 0.202 4.4 07/22/09 39,512,629.4 276.7 1,840.02,856.1 267 60.00 4.057 0.185 4.4 07/22/09 38,391,798.0 276.0 1,840.02,712.5 254 60.00 3.886 0.169 3.6 07/22/09 38,427,127.4 274.9 1,840.02,735.8 252 60.00 3.856 0.169 3.6 07/22/09 35,278,432.6 269.4 1,840.02,454.1 224 60.00 3.229 0.127 4.1 07/22/09 29,393,563.9 266.3 1,840.0 1,996.9 180 60.00 3.307 0.106 3.4 07/22/09 28,426,794.8 265.9 1,840.0 1,962.1 181 60.00 3.707 0.116 3.4 07/22/09 28,340,729.4 264.1 1,840.0 1,956.1 176 60.00 3.074 0.096 3.7 07/22/09 26,528,970.5 264.8 1,840.0 1,715.7 163 60.00 3.280 0.090 3.7 07/22/09 26,643,344.2 265.8 1,840.0 1,824.5 161 60.00 3.372 0.098 4.0 07/22/09 28,649,959.8 268.51,840.0 1,946.3 180 60.00 3.399 0.106 07/21/09 28,629,214.7 267.0 1,840.0 1,991.6 180 60.00 3.588 0.114

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 2.7 2.6 07/25/09 26,505,688.9 265.0 1,840.0 1,800.7 167 60.00 2.480 0.071 2.9 07/24/09 27,425,732.9 267.51,840.0 1,878.1 174 60.00 2.369 0.071 3.5 07/24/09 29,075,560.2 270.1 1,840.0 1,991.1 185 60.00 2.643 0.084 4.1 07/24/09 33,339,778.6 276.0 1,840.02,337.4 220 60.00 3.115 0.116 4.5 07/24/09 38,041,814.6 279.4 1,840.02,729.1 258 60.00 3.566 0.156 4.5 07/24/09 38,751,725.2 279.7 1,840.02,801.1 266 60.00 3.885 0.174 4.5 07/24/09 40,117,254.4 281.7 1,840.02,899.8 275 60.00 3.885 0.180 4.5 07/24/09 40,725,743.1 283.0 1,840.02,943.8 280 60.00 3.885 0.183 4.4 07/24/09 41,863,655.1 284.3 1,840.03,026.0 289 60.00 3.885 0.188 4.3 07/24/09 41,493,470.2 282.51,840.03,044.3 288 60.00 3.742 0.182 4.4 07/24/09 40,294,007.4 280.2 1,840.02,956.4 275 60.00 3.657 0.173 3.8 07/24/09 36,871,443.0 272.8 1,840.02,665.1 242 60.00 3.798 0.162 4.1 07/24/09 29,395,412.4 267.9 1,840.02,092.8 186 60.00 3.331 0.111 3.7 07/24/09 29,190,197.3 267.9 1,840.0 1,998.9 185 60.00 3.736 0.119 3.7 07/24/09 25,843,804.7 266.1 1,840.0 1,811.9 159 60.00 3.293 0.095 3.8 07/24/09 27,121,753.7 270.1 1,840.0 1,857.3 174 60.00 3.372 0.100 3.4 07/24/09 33,112,803.1 271.6 1,840.02,285.5 219 60.00 3.435 0.126 3.3 07/24/09 35,662,690.3 276.0 1,840.02,577.8 240 60.00 2.935 0.121 3.1 07/24/09 34,197,136.5 269.7 1,840.02,471.8 218 60.00 2.849 0.113 3.2 07/24/09 26,791,382.1 265.6 1,840.0 1,863.7 166 60.00 2.781 0.083 2.8 07/24/09 26,021,510.4 263.51,840.0 1,852.7 162 60.00 2.805 0.083 2.8 07/24/09 24,975,875.4 265.1 1,840.0 1,737.5 157 60.00 2.512 0.070 3.0 07/24/09 25,397,304.7 265.1 1,840.0 1,794.4 155 60.00 2.473 0.071 3.0 07/24/09 25,031,096.1 266.6 1,840.0 1,741.3 152 60.00 2.691 0.075 3.2 07/24/09 28,702,921.6 267.7 1,840.0 1,996.7 180 60.00 2.691 0.086 2.9 07/23/09 30,182,871.6 269.7 1,840.02,083.3 193 60.00 2.893 0.096 3.4 07/23/09 31,516,845.9 273.6 1,840.02,209.6 206 60.00 2.581 0.091 3.7 07/23/09 39,320,916.2 279.6 1,840.02,799.5 263 60.00 2.980 0.133 3.7 07/23/09 40,170,515.5 281.1 1,840.02,881.8 272 60.00 3.218 0.148 4.2 07/23/09 40,635,890.8 281.7 1,840.02,915.2 275 60.00 3.218 0.150 4.5 07/23/09 40,802,248.2 282.4 1,840.02,927.1 279 60.00 3.653 0.171 4.6 07/23/09 41,702,581.8 283.0 1,840.03,037.1 287 60.00 3.856 0.187 4.5 07/23/09 41,576,452.9 282.2 1,840.02,982.6 283 60.00 4.001 0.191 4.4 07/23/09 41,448,863.5 282.0 1,840.02,973.5 282 60.00 3.914 0.186 4.3 07/23/09 41,426,238.0 281.8 1,840.02,971.9 282 60.00 3.827 0.182 4.1 07/23/09 41,702,156.1 280.9 1,840.02,991.7 282 60.00 3.740 0.179 07/23/09 41,702,430.9 280.7 1,840.02,991.7 282 60.00 3.566 0.171

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 2.7 2.8 07/26/09 39,628,976.7 280.3 1,840.02,886.0 268 60.00 2.313 0.107 2.6 07/26/09 39,972,056.7 281.1 1,840.02,911.0 272 60.00 2.399 0.112 2.5 07/26/09 38,928,749.2 278.4 1,840.02,835.0 263 60.00 2.228 0.101 2.4 07/26/09 36,753,148.0 275.51,840.02,636.6 243 60.00 2.175 0.092 2.5 07/26/09 33,134,627.3 268.6 1,840.02,359.1 209 60.00 2.103 0.079 2.5 07/26/09 27,380,102.5 267.4 1,840.0 1,845.2 173 60.00 2.315 0.068 2.2 07/26/09 30,621,950.2 268.0 1,840.02,096.9 193 60.00 2.278 0.076 2.3 07/26/09 28,843,118.9 264.3 1,840.0 1,990.8 178 60.00 1.989 0.063 1.6 07/26/09 24,915,930.2 262.6 1,840.0 1,733.3 152 60.00 2.063 0.057 1.4 07/26/09 24,794,852.4 262.4 1,840.0 1,684.4 151 60.00 1.470 0.040 1.4 07/26/09 25,229,892.8 263.6 1,840.0 1,672.9 152 60.00 1.318 0.035 1.9 07/26/09 25,524,936.1 264.2 1,840.0 1,692.4 151 60.00 1.318 0.036 1.9 07/26/09 25,268,009.2 264.8 1,840.0 1,702.8 151 60.00 1.759 0.048 2.4 07/26/09 25,069,115.9 264.8 1,840.0 1,730.3 155 60.00 1.718 0.048 2.3 07/25/09 25,882,227.9 266.1 1,840.0 1,786.4 161 60.00 2.170 0.062 2.6 07/25/09 27,615,890.0 266.9 1,840.0 1,936.1 173 60.00 2.047 0.063 2.7 07/25/09 28,725,653.2 270.6 1,840.0 1,982.7 183 60.00 2.351 0.075 2.4 07/25/09 36,329,883.8 276.51,840.02,547.0 238 60.00 2.403 0.098 2.4 07/25/09 36,717,456.8 273.9 1,840.02,594.1 236 60.00 2.120 0.088 3.0 07/25/09 34,337,976.6 275.51,840.02,388.7 221 60.00 2.153 0.082 3.5 07/25/09 36,298,372.4 278.6 1,840.02,584.3 241 60.00 2.629 0.109 3.7 07/25/09 40,039,740.4 283.51,840.02,916.0 273 60.00 2.999 0.140 3.7 07/25/09 40,140,891.8 282.8 1,840.02,923.3 274 60.00 3.170 0.148 4.0 07/25/09 41,218,797.4 282.2 1,840.03,001.8 281 60.00 3.170 0.152 4.5 07/25/09 39,207,777.6 279.0 1,840.02,834.1 263 60.00 3.453 0.156 4.3 07/25/09 38,838,641.1 279.8 1,840.02,786.3 260 60.00 3.914 0.174 4.4 07/25/09 38,257,182.8 280.0 1,840.02,744.5 255 60.00 3.740 0.164 4.5 07/25/09 37,201,103.0 276.8 1,840.02,668.8 244 60.00 3.827 0.163 4.3 07/25/09 35,152,647.1 274.6 1,840.02,502.7 230 60.00 3.944 0.158 3.3 07/25/09 35,995,142.9 271.8 1,840.02,543.1 233 60.00 3.798 0.154 3.4 07/25/09 28,716,980.0 266.6 1,840.0 1,966.5 180 60.00 3.007 0.095 2.9 07/25/09 30,945,457.9 266.6 1,840.02,102.2 196 60.00 3.123 0.105 2.5 07/25/09 27,368,321.1 263.3 1,840.0 1,859.2 168 60.00 2.664 0.079 2.4 07/25/09 25,972,346.9 264.4 1,840.0 1,778.5 160 60.00 2.278 0.065 2.2 07/25/09 25,463,753.3 264.0 1,840.0 1,702.2 154 60.00 2.240 0.061 2.6 07/25/09 25,305,015.2 264.8 1,840.0 1,691.6 151 60.00 2.054 0.056 07/25/09 26,581,458.9 264.51,840.0 1,820.2 166 60.00 2.369 0.069

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 1.6 1.6 07/28/09 26,800,682.2 263.9 1,840.0 1,777.0 160 60.00 1.506 0.043 1.6 07/28/09 26,130,099.6 264.3 1,840.0 1,704.1 157 60.00 1.531 0.042 1.4 07/28/09 28,247,551.2 266.6 1,840.0 1,934.4 175 60.00 1.458 0.045 1.5 07/27/09 27,241,608.8 266.3 1,840.0 1,895.1 168 60.00 1.256 0.038 1.6 07/27/09 30,419,863.1 271.7 1,840.02,083.1 197 60.00 1.367 0.046 1.8 07/27/09 38,260,469.7 277.7 1,840.02,723.9 252 60.00 1.402 0.061 1.9 07/27/09 39,800,316.7 279.8 1,840.02,855.2 265 60.00 1.566 0.071 2.0 07/27/09 41,503,985.5 281.1 1,840.02,977.5 277 60.00 1.653 0.079 1.9 07/27/09 41,184,848.5 281.7 1,840.02,954.6 279 60.00 1.740 0.082 1.8 07/27/09 42,092,720.2 281.51,840.03,042.6 287 60.00 1.640 0.080 1.7 07/27/09 41,458,526.1 280.9 1,840.03,019.3 283 60.00 1.542 0.074 1.7 07/27/09 41,522,545.4 282.4 1,840.03,024.0 282 60.00 1.457 0.070 1.8 07/27/09 41,699,531.9 283.0 1,840.03,036.8 282 60.00 1.457 0.071 1.9 07/27/09 41,951,119.1 282.9 1,840.03,055.1 282 60.00 1.542 0.075 1.9 07/27/09 41,592,459.9 281.4 1,840.03,051.6 282 60.00 1.616 0.079 1.8 07/27/09 41,640,088.2 280.51,840.03,032.5 282 60.00 1.628 0.079 2.0 07/27/09 41,513,615.4 280.6 1,840.03,045.9 282 60.00 1.531 0.075 1.9 07/27/09 41,656,625.1 280.6 1,840.03,056.4 282 60.00 1.701 0.083 1.9 07/27/09 40,333,971.1 278.0 1,840.02,937.4 270 60.00 1.628 0.076 1.3 07/27/09 38,807,891.9 276.2 1,840.02,784.1 254 60.00 1.653 0.074 1.4 07/27/09 34,733,633.7 267.6 1,840.02,435.2 218 60.00 1.157 0.045 0.9 07/27/09 25,991,519.8 263.4 1,840.0 1,765.8 161 60.00 1.286 0.036 1.0 07/27/09 26,399,387.1 264.51,840.0 1,793.4 162 60.00 0.827 0.024 1.0 07/27/09 25,796,355.8 263.9 1,840.0 1,724.4 154 60.00 0.933 0.026 1.6 07/27/09 25,620,787.3 263.9 1,840.0 1,670.9 152 60.00 0.957 0.026 1.7 07/27/09 24,823,288.0 263.3 1,840.0 1,686.3 151 60.00 1.470 0.040 1.8 07/27/09 24,628,038.4 264.6 1,840.0 1,659.7 152 60.00 1.574 0.042 1.8 07/26/09 27,404,913.7 265.51,840.0 1,861.8 170 60.00 1.653 0.049 2.0 07/26/09 26,777,735.4 268.4 1,840.0 1,804.6 169 60.00 1.667 0.048 2.2 07/26/09 34,296,061.9 274.7 1,840.02,423.1 229 60.00 1.766 0.068 1.8 07/26/09 38,642,159.7 278.0 1,840.02,772.1 262 60.00 1.914 0.085 2.1 07/26/09 38,632,867.0 278.1 1,840.02,750.5 259 60.00 1.578 0.069 2.3 07/26/09 40,210,573.1 280.9 1,840.02,862.8 271 60.00 1.841 0.084 2.7 07/26/09 39,843,011.5 281.7 1,840.02,901.6 268 60.00 1.971 0.091 2.8 07/26/09 40,070,025.4 282.3 1,840.02,961.7 275 60.00 2.279 0.108 2.8 07/26/09 40,646,060.2 280.9 1,840.02,982.2 277 60.00 2.381 0.114 07/26/09 39,062,312.9 279.8 1,840.02,844.7 265 60.00 2.399 0.109

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 2.9 3.0 07/29/09 41,154,229.9 280.51,840.02,997.1 280 60.00 2.485 0.119 3.0 07/29/09 40,789,531.3 279.6 1,840.02,970.6 274 60.00 2.571 0.122 2.8 07/29/09 41,507,786.7 278.9 1,840.03,000.3 278 60.00 2.590 0.124 2.9 07/29/09 39,884,478.3 278.6 1,840.02,904.6 269 60.00 2.399 0.111 2.6 07/29/09 41,840,968.4 278.9 1,840.03,024.4 282 60.00 2.504 0.121 2.5 07/29/09 38,810,861.3 273.0 1,840.02,657.7 252 60.00 2.369 0.101 2.3 07/29/09 32,915,783.5 267.8 1,840.02,307.7 210 60.00 2.225 0.082 2.5 07/29/09 32,040,513.1 267.7 1,840.02,246.4 205 60.00 2.047 0.074 1.7 07/29/09 32,698,650.2 269.0 1,840.02,221.4 207 60.00 2.296 0.082 1.8 07/29/09 30,922,554.0 264.4 1,840.02,067.1 187 60.00 1.587 0.052 2.1 07/29/09 25,681,604.6 261.9 1,840.0 1,688.9 153 60.00 1.708 0.046 1.8 07/29/09 26,173,772.5 262.0 1,840.0 1,721.2 159 60.00 1.993 0.055 1.9 07/29/09 25,120,355.1 262.9 1,840.0 1,651.9 153 60.00 1.708 0.045 2.0 07/29/09 25,370,968.4 263.3 1,840.0 1,723.6 152 60.00 1.745 0.048 1.7 07/29/09 25,996,760.3 264.51,840.0 1,681.3 155 60.00 1.930 0.052 1.6 07/29/09 27,735,063.2 264.3 1,840.0 1,839.0 170 60.00 1.600 0.047 1.6 07/28/09 25,865,277.4 265.6 1,840.0 1,757.1 160 60.00 1.470 0.041 1.9 07/28/09 29,869,347.7 270.2 1,840.02,094.1 190 60.00 1.424 0.048 2.0 07/28/09 35,083,588.2 275.8 1,840.02,516.9 235 60.00 1.653 0.067 1.8 07/28/09 39,948,159.6 277.7 1,840.02,909.3 272 60.00 1.714 0.080 1.9 07/28/09 39,492,949.6 278.0 1,840.02,854.7 268 60.00 1.554 0.071 2.0 07/28/09 38,677,418.9 277.7 1,840.02,795.7 259 60.00 1.640 0.073 2.2 07/28/09 38,594,969.3 280.51,840.02,789.7 259 60.00 1.727 0.077 2.1 07/28/09 41,310,312.3 281.4 1,840.02,986.0 283 60.00 1.899 0.091 1.9 07/28/09 40,018,328.3 278.51,840.02,892.6 271 60.00 1.813 0.084 2.2 07/28/09 39,858,760.9 281.2 1,840.02,859.5 270 60.00 1.653 0.076 2.4 07/28/09 41,369,683.7 282.2 1,840.02,945.4 279 60.00 1.928 0.091 2.5 07/28/09 41,498,539.7 283.6 1,840.02,932.0 279 60.00 2.120 0.099 2.5 07/28/09 41,659,364.5 282.7 1,840.02,988.6 285 60.00 2.175 0.104 2.5 07/28/09 41,726,660.7 281.6 1,840.03,038.8 286 60.00 2.142 0.104 2.2 07/28/09 40,849,538.0 277.51,840.02,952.7 277 60.00 2.158 0.102 2.1 07/28/09 39,099,024.0 275.7 1,840.02,762.4 259 60.00 1.943 0.086 1.6 07/28/09 37,708,676.9 272.1 1,840.02,643.7 240 60.00 1.869 0.079 1.4 07/28/09 30,958,853.4 265.2 1,840.02,086.4 188 60.00 1.481 0.049 1.8 07/28/09 27,009,773.2 262.6 1,840.0 1,790.9 161 60.00 1.318 0.038 1.7 07/28/09 26,099,598.1 265.0 1,840.0 1,744.7 159 60.00 1.680 0.047 07/28/09 29,367,379.6 265.4 1,840.0 1,963.1 177 60.00 1.587 0.050

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 1.8 1.8 07/31/09 28,539,183.8 264.6 1,840.0 1,938.8 170 60.00 1.653 0.051 1.7 07/31/09 26,558,319.4 264.2 1,840.0 1,760.9 154 60.00 1.694 0.048 2.1 07/31/09 26,736,476.1 264.2 1,840.0 1,772.7 154 60.00 1.600 0.045 2.0 07/31/09 25,921,984.7 263.6 1,840.0 1,761.0 156 60.00 1.929 0.054 1.8 07/31/09 25,413,655.2 263.6 1,840.0 1,726.5 152 60.00 1.837 0.051 1.5 07/30/09 27,077,323.0 265.8 1,840.0 1,854.2 167 60.00 1.640 0.049 2.1 07/30/09 27,425,381.5 267.4 1,840.0 1,878.0 168 60.00 1.367 0.041 2.3 07/30/09 31,934,129.7 274.6 1,840.02,169.4 204 60.00 1.929 0.067 2.6 07/30/09 37,862,861.7 274.51,840.02,675.1 241 60.00 2.031 0.087 3.7 07/30/09 29,656,392.4 269.7 1,840.02,030.8 184 60.00 2.369 0.077 3.2 07/30/09 34,037,011.2 276.1 1,840.02,386.3 226 60.00 3.293 0.126 3.2 07/30/09 40,598,341.9 279.4 1,840.02,912.5 274 60.00 2.783 0.130 3.3 07/30/09 41,207,203.9 280.8 1,840.02,911.4 278 60.00 2.826 0.132 3.2 07/30/09 40,192,958.0 280.1 1,840.02,839.7 269 60.00 2.915 0.132 3.1 07/30/09 40,164,750.1 279.51,840.02,837.7 269 60.00 2.826 0.128 3.1 07/30/09 40,682,750.0 278.8 1,840.02,896.5 275 60.00 2.717 0.126 3.1 07/30/09 40,345,037.3 278.7 1,840.02,850.5 270 60.00 2.738 0.125 2.9 07/30/09 40,182,360.7 279.0 1,840.02,817.1 269 60.00 2.759 0.124 2.5 07/30/09 39,440,277.9 275.4 1,840.02,786.5 258 60.00 2.561 0.114 2.4 07/30/09 32,679,370.1 267.6 1,840.02,237.8 202 60.00 2.278 0.082 2.5 07/30/09 26,729,477.7 266.0 1,840.0 1,772.2 156 60.00 2.259 0.064 3.1 07/30/09 30,656,227.5 269.2 1,840.02,049.3 188 60.00 2.334 0.076 2.9 07/30/09 27,480,941.7 264.9 1,840.0 1,866.9 165 60.00 2.847 0.085 2.4 07/30/09 27,910,218.7 264.6 1,840.0 1,896.1 172 60.00 2.664 0.081 2.4 07/30/09 26,436,184.4 263.1 1,840.0 1,810.3 162 60.00 2.187 0.063 2.1 07/30/09 25,409,935.1 262.6 1,840.0 1,726.2 156 60.00 2.204 0.061 2.1 07/30/09 25,918,001.5 263.4 1,840.0 1,760.7 156 60.00 1.929 0.054 2.1 07/30/09 25,809,758.3 264.0 1,840.0 1,767.4 156 60.00 1.914 0.054 2.1 07/30/09 25,249,006.6 264.8 1,840.0 1,729.0 154 60.00 1.914 0.053 2.2 07/29/09 26,044,627.6 264.6 1,840.0 1,783.5 158 60.00 1.914 0.055 2.5 07/29/09 24,469,683.5 264.9 1,840.0 1,728.9 154 60.00 1.943 0.054 2.9 07/29/09 28,414,652.1 269.8 1,840.0 1,976.7 181 60.00 2.242 0.071 2.8 07/29/09 36,389,069.5 275.1 1,840.02,630.3 241 60.00 2.504 0.105 3.0 07/29/09 32,961,976.2 273.0 1,840.02,382.6 214 60.00 2.417 0.092 3.3 07/29/09 37,101,272.3 277.8 1,840.02,681.8 247 60.00 2.590 0.111 3.1 07/29/09 40,825,351.8 281.2 1,840.02,973.1 277 60.00 2.828 0.134 07/29/09 41,082,284.9 279.6 1,840.02,969.5 281 60.00 2.676 0.127

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 1.9 1.4 08/01/09 30,389,375.8 267.6 1,840.02,064.5 196 60.00 1.745 0.058 1.3 08/01/09 31,589,741.7 267.0 1,840.02,197.6 198 60.00 1.256 0.044 1.5 08/01/09 28,970,363.2 267.1 1,840.02,015.3 181 60.00 1.166 0.038 1.4 08/01/09 29,890,018.3 272.1 1,840.02,128.0 194 60.00 1.315 0.045 1.6 08/01/09 35,791,983.3 271.9 1,840.02,606.6 232 60.00 1.200 0.050 1.7 08/01/09 35,155,809.1 275.4 1,840.02,541.2 235 60.00 1.381 0.056 1.7 08/01/09 38,636,976.4 275.8 1,840.02,792.8 257 60.00 1.468 0.066 1.6 08/01/09 37,962,985.9 275.2 1,840.02,702.8 253 60.00 1.490 0.064 1.5 08/01/09 39,697,614.0 276.0 1,840.02,869.5 268 60.00 1.381 0.063 1.2 08/01/09 38,982,189.6 275.51,840.02,775.3 259 60.00 1.315 0.058 1.2 08/01/09 35,115,663.6 269.1 1,840.02,519.2 223 60.00 1.044 0.042 1.2 08/01/09 28,457,613.5 265.1 1,840.0 1,995.2 179 60.00 1.068 0.034 1.0 08/01/09 25,738,973.8 263.0 1,840.0 1,832.5 161 60.00 1.052 0.031 1.1 08/01/09 25,370,671.4 264.2 1,840.0 1,778.7 158 60.00 0.890 0.025 1.1 08/01/09 24,992,028.9 264.1 1,840.0 1,725.0 153 60.00 0.994 0.027 1.1 08/01/09 25,868,122.5 263.8 1,840.0 1,813.6 159 60.00 0.979 0.028 1.1 08/01/09 24,752,088.8 263.1 1,840.0 1,721.9 154 60.00 0.987 0.027 1.2 08/01/09 24,771,680.2 265.0 1,840.0 1,750.2 155 60.00 0.972 0.027 1.2 07/31/09 27,121,281.1 267.6 1,840.0 1,916.2 170 60.00 1.060 0.032 1.3 07/31/09 27,253,950.6 268.6 1,840.0 1,895.9 170 60.00 1.076 0.033 1.5 07/31/09 32,045,185.6 270.9 1,840.02,281.5 205 60.00 1.139 0.042 1.4 07/31/09 34,096,534.9 275.3 1,840.02,409.0 226 60.00 1.325 0.051 1.3 07/31/09 39,757,692.7 277.1 1,840.02,873.8 269 60.00 1.209 0.056 1.7 07/31/09 38,790,217.5 279.3 1,840.02,803.8 261 60.00 1.122 0.050 2.1 07/31/09 41,407,101.8 281.7 1,840.02,970.5 282 60.00 1.479 0.070 2.3 07/31/09 42,670,849.9 283.8 1,840.03,061.2 292 60.00 1.827 0.089 1.9 07/31/09 43,004,947.4 283.4 1,840.03,061.8 291 60.00 2.016 0.099 1.9 07/31/09 41,759,931.0 280.3 1,840.02,995.8 285 60.00 1.653 0.079 2.1 07/31/09 41,564,255.2 281.0 1,840.03,004.4 284 60.00 1.640 0.079 1.8 07/31/09 42,109,585.0 280.4 1,840.03,043.8 287 60.00 1.813 0.088 2.0 07/31/09 40,610,689.8 278.4 1,840.02,913.4 275 60.00 1.566 0.073 2.1 07/31/09 40,890,297.0 278.0 1,840.02,889.0 276 60.00 1.766 0.082 2.1 07/31/09 40,247,764.0 278.0 1,840.02,799.9 270 60.00 1.884 0.084 2.0 07/31/09 42,346,418.7 279.51,840.03,014.9 282 60.00 1.841 0.089 1.8 07/31/09 40,474,535.6 275.8 1,840.02,903.6 267 60.00 1.740 0.081 1.8 07/31/09 34,632,387.7 268.1 1,840.02,409.2 213 60.00 1.615 0.062 07/31/09 28,324,507.7 264.3 1,840.0 1,924.3 165 60.00 1.653 0.051

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 2.1 2.1 08/03/09 34,011,918.7 267.0 1,840.02,384.5 213 60.00 1.869 0.071 2.3 08/03/09 26,546,449.8 265.2 1,840.0 1,789.0 160 60.00 1.944 0.056 2.1 08/03/09 29,477,017.9 266.0 1,840.02,050.6 188 60.00 2.063 0.068 1.9 08/03/09 28,206,782.3 262.7 1,840.0 1,962.2 176 60.00 1.884 0.059 2.0 08/03/09 24,901,000.9 262.6 1,840.0 1,678.1 153 60.00 1.759 0.047 2.0 08/03/09 25,202,866.4 264.1 1,840.0 1,698.5 153 60.00 1.852 0.050 2.1 08/03/09 27,173,566.6 265.7 1,840.0 1,860.8 166 60.00 1.822 0.054 2.3 08/02/09 26,336,972.9 263.9 1,840.0 1,817.8 159 60.00 1.899 0.055 2.4 08/02/09 24,959,111.4 263.4 1,840.0 1,695.6 152 60.00 2.113 0.057 2.2 08/02/09 25,924,207.5 266.4 1,840.0 1,775.2 160 60.00 2.187 0.062 2.0 08/02/09 32,342,860.0 272.4 1,840.02,285.1 209 60.00 1.943 0.071 2.1 08/02/09 36,254,310.0 272.7 1,840.02,561.4 233 60.00 1.766 0.072 2.4 08/02/09 35,425,274.2 273.1 1,840.02,502.9 227 60.00 1.855 0.074 2.5 08/02/09 36,655,241.3 275.0 1,840.02,589.8 239 60.00 2.120 0.088 2.6 08/02/09 37,464,387.1 276.1 1,840.02,646.9 247 60.00 2.208 0.093 2.3 08/02/09 38,517,821.8 276.1 1,840.02,721.4 254 60.00 2.296 0.100 2.4 08/02/09 38,119,716.9 275.9 1,840.02,714.0 247 60.00 2.016 0.087 2.0 08/02/09 37,848,319.1 274.7 1,840.02,674.0 242 60.00 2.120 0.091 2.1 08/02/09 36,311,638.2 273.51,840.02,545.8 229 60.00 1.780 0.072 2.0 08/02/09 37,328,903.6 274.51,840.02,617.1 240 60.00 1.869 0.078 1.8 08/02/09 36,385,852.3 272.0 1,840.02,570.8 230 60.00 1.766 0.073 1.8 08/02/09 31,760,889.6 269.0 1,840.02,244.0 198 60.00 1.590 0.057 1.5 08/02/09 33,925,674.1 268.2 1,840.02,396.9 215 60.00 1.590 0.061 1.4 08/02/09 29,377,285.2 265.6 1,840.02,059.6 186 60.00 1.335 0.044 1.5 08/02/09 25,432,655.4 263.51,840.0 1,796.9 157 60.00 1.236 0.036 1.4 08/02/09 24,725,788.6 263.0 1,840.0 1,720.1 150 60.00 1.345 0.037 1.2 08/02/09 25,199,625.0 262.51,840.0 1,753.0 156 60.00 1.256 0.035 1.4 08/02/09 24,679,340.3 263.4 1,840.0 1,716.8 152 60.00 1.076 0.030 1.5 08/02/09 24,601,658.7 264.0 1,840.0 1,684.7 152 60.00 1.276 0.034 1.8 08/02/09 25,019,649.7 263.8 1,840.0 1,740.5 153 60.00 1.345 0.037 1.8 08/02/09 24,703,541.7 263.3 1,840.0 1,745.4 156 60.00 1.590 0.044 2.0 08/01/09 24,417,849.9 263.3 1,840.0 1,725.2 153 60.00 1.590 0.044 2.1 08/01/09 26,560,685.9 265.6 1,840.0 1,804.4 168 60.00 1.837 0.053 2.1 08/01/09 29,102,029.5 268.6 1,840.02,008.7 189 60.00 1.899 0.061 1.7 08/01/09 35,900,478.7 274.0 1,840.02,536.4 238 60.00 1.855 0.075 1.6 08/01/09 33,079,718.3 270.3 1,840.02,337.2 211 60.00 1.501 0.056 08/01/09 32,034,275.8 268.7 1,840.02,193.6 202 60.00 1.458 0.051

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 2.3 1.9 08/04/09 38,723,267.5 276.9 1,840.02,756.9 260 60.00 2.016 0.089 2.1 08/04/09 39,517,771.9 279.2 1,840.02,835.0 267 60.00 1.653 0.075 2.2 08/04/09 40,965,980.4 281.2 1,840.02,961.1 279 60.00 1.813 0.086 2.1 08/04/09 41,518,547.2 282.0 1,840.03,023.7 282 60.00 1.885 0.091 2.2 08/04/09 41,265,662.9 281.7 1,840.03,027.7 282 60.00 1.786 0.086 2.2 08/04/09 40,777,302.3 280.8 1,840.02,991.8 282 60.00 1.871 0.090 2.1 08/04/09 40,785,003.3 280.9 1,840.02,970.2 282 60.00 1.885 0.090 2.2 08/04/09 40,959,702.2 281.9 1,840.02,983.0 282 60.00 1.799 0.086 2.1 08/04/09 40,539,289.9 281.6 1,840.02,974.3 282 60.00 1.871 0.089 1.9 08/04/09 40,061,737.1 281.0 1,840.02,982.9 279 60.00 1.760 0.084 2.0 08/04/09 40,044,862.0 279.7 1,840.02,981.6 282 60.00 1.592 0.076 2.3 08/04/09 39,842,826.9 280.51,840.02,944.9 278 60.00 1.688 0.080 2.2 08/04/09 38,865,007.8 280.0 1,840.02,872.6 266 60.00 1.942 0.089 2.1 08/04/09 39,600,675.9 279.0 1,840.02,905.5 267 60.00 1.871 0.087 1.9 08/04/09 35,232,817.8 270.9 1,840.02,527.6 228 60.00 1.827 0.074 1.9 08/04/09 32,073,721.7 268.8 1,840.02,266.1 208 60.00 1.678 0.061 1.9 08/04/09 28,613,704.8 267.1 1,840.0 1,943.9 171 60.00 1.745 0.054 1.8 08/04/09 28,408,489.6 266.3 1,840.0 1,945.3 167 60.00 1.731 0.054 1.9 08/04/09 28,275,640.4 267.9 1,840.0 1,920.9 173 60.00 1.653 0.051 1.8 08/04/09 29,382,449.5 268.9 1,840.02,059.9 189 60.00 1.691 0.056 2.2 08/03/09 31,960,268.9 273.1 1,840.02,258.0 209 60.00 1.590 0.057 2.5 08/03/09 31,507,125.2 273.4 1,840.02,208.9 203 60.00 1.958 0.069 2.5 08/03/09 38,633,562.0 280.4 1,840.02,771.6 258 60.00 2.175 0.096 2.5 08/03/09 41,299,987.9 284.1 1,840.02,962.8 276 60.00 2.175 0.103 2.4 08/03/09 41,833,452.8 285.2 1,840.03,001.1 282 60.00 2.175 0.104 2.5 08/03/09 41,862,825.0 285.6 1,840.02,980.5 282 60.00 2.103 0.100 2.3 08/03/09 41,765,138.3 284.8 1,840.02,996.2 282 60.00 2.175 0.104 2.6 08/03/09 41,998,242.7 286.2 1,840.03,012.9 282 60.00 2.001 0.096 2.5 08/03/09 42,267,427.7 286.0 1,840.03,009.2 283 60.00 2.279 0.110 2.5 08/03/09 42,391,545.2 285.6 1,840.03,041.2 282 60.00 2.175 0.106 2.5 08/03/09 41,969,802.3 283.51,840.03,033.7 282 60.00 2.158 0.105 2.4 08/03/09 41,978,197.4 281.0 1,840.03,034.3 283 60.00 2.158 0.105 2.5 08/03/09 41,957,643.1 279.7 1,840.03,032.8 282 60.00 2.072 0.100 2.7 08/03/09 40,736,941.4 279.1 1,840.02,900.3 273 60.00 2.191 0.102 2.6 08/03/09 41,279,275.6 279.2 1,840.02,961.3 278 60.00 2.349 0.111 2.2 08/03/09 39,213,689.2 274.3 1,840.02,834.5 261 60.00 2.245 0.102 08/03/09 35,087,095.9 271.0 1,840.02,498.0 227 60.00 1.928 0.077

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 2.7 2.6 08/06/09 40,554,019.4 280.1 1,840.02,975.4 282 60.00 2.296 0.109 1.9 08/06/09 39,384,909.3 276.4 1,840.02,868.3 270 60.00 2.228 0.102 1.7 08/06/09 37,988,525.7 273.4 1,840.02,745.9 251 60.00 1.640 0.072 1.9 08/06/09 31,485,287.7 265.0 1,840.02,190.3 191 60.00 1.525 0.053 2.0 08/06/09 27,237,342.1 263.8 1,840.0 1,850.3 164 60.00 1.745 0.052 1.8 08/06/09 25,991,487.6 263.4 1,840.0 1,765.7 156 60.00 1.837 0.052 1.7 08/06/09 25,891,419.4 265.3 1,840.0 1,758.9 154 60.00 1.653 0.047 1.6 08/06/09 28,886,114.2 266.51,840.02,025.2 177 60.00 1.513 0.049 1.7 08/06/09 29,309,887.6 268.8 1,840.02,070.8 187 60.00 1.413 0.047 1.8 08/05/09 31,660,341.6 269.1 1,840.02,271.3 203 60.00 1.479 0.054 2.0 08/05/09 30,446,792.6 271.2 1,840.02,118.1 195 60.00 1.615 0.055 2.2 08/05/09 37,467,916.2 278.3 1,840.02,687.9 251 60.00 1.740 0.075 2.4 08/05/09 39,649,720.2 279.1 1,840.02,866.0 267 60.00 1.899 0.087 2.6 08/05/09 40,225,269.6 278.7 1,840.02,907.6 269 60.00 2.072 0.096 2.6 08/05/09 38,186,515.3 279.0 1,840.02,718.7 252 60.00 2.279 0.099 2.7 08/05/09 40,647,157.6 280.8 1,840.02,916.0 273 60.00 2.262 0.105 2.7 08/05/09 41,480,582.8 281.8 1,840.03,020.9 285 60.00 2.313 0.112 2.7 08/05/09 42,033,165.6 281.8 1,840.03,083.9 287 60.00 2.296 0.113 2.7 08/05/09 42,015,777.8 281.7 1,840.03,059.9 287 60.00 2.313 0.113 2.4 08/05/09 41,805,570.5 281.3 1,840.03,067.3 287 60.00 2.296 0.113 2.1 08/05/09 41,675,559.5 279.3 1,840.03,057.8 286 60.00 2.041 0.100 2.2 08/05/09 41,188,943.8 279.6 1,840.02,977.2 281 60.00 1.813 0.086 2.4 08/05/09 41,063,837.9 279.51,840.02,968.2 277 60.00 1.899 0.090 2.6 08/05/09 40,737,538.6 278.6 1,840.02,922.5 272 60.00 2.088 0.098 2.4 08/05/09 40,383,877.7 278.2 1,840.02,919.1 271 60.00 2.245 0.105 2.3 08/05/09 39,493,021.8 276.0 1,840.02,811.7 262 60.00 2.103 0.095 2.0 08/05/09 34,779,480.5 269.6 1,840.02,457.2 220 60.00 2.031 0.080 1.9 08/05/09 30,045,849.8 266.51,840.02,122.8 191 60.00 1.766 0.060 2.1 08/05/09 29,024,927.7 265.6 1,840.02,034.9 186 60.00 1.691 0.055 2.1 08/05/09 27,190,287.1 263.0 1,840.0 1,891.5 170 60.00 1.884 0.057 2.0 08/05/09 25,246,825.4 262.1 1,840.0 1,728.9 156 60.00 1.914 0.053 2.0 08/05/09 25,328,196.0 263.51,840.0 1,706.9 152 60.00 1.852 0.051 1.8 08/05/09 26,734,190.9 264.6 1,840.0 1,801.6 158 60.00 1.852 0.053 2.0 08/04/09 27,730,284.8 266.4 1,840.0 1,868.8 167 60.00 1.667 0.050 2.4 08/04/09 29,313,308.2 270.3 1,840.02,007.3 183 60.00 1.822 0.058 2.3 08/04/09 37,266,576.2 277.3 1,840.02,612.7 245 60.00 2.136 0.089 08/04/09 40,063,618.0 278.7 1,840.02,874.2 268 60.00 2.001 0.092

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C ST ST STC 06:00 ST ST ST 07:00 ST ST ST 08:00 ST ST ST 09:00 ST ST STC 10:00 C 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 3.5 3.9 08/07/09 34,624,587.9 274.9 1,840.02,465.1 231 60.00 3.068 0.121 3.6 08/07/09 36,812,384.8 276.8 1,840.02,640.9 247 60.00 3.392 0.143 3.6 08/07/09 34,616,313.1 272.2 1,840.02,483.3 231 60.00 3.131 0.124 3.4 08/07/09 34,785,377.4 274.8 1,840.02,514.4 235 60.00 3.108 0.125 3.2 08/07/09 38,366,405.4 276.6 1,840.02,835.7 264 60.00 2.870 0.130 3.6 08/07/09 37,400,058.4 277.7 1,840.02,744.0 254 60.00 2.722 0.119 3.5 08/07/09 40,466,516.7 280.8 1,840.02,991.0 280 60.00 3.039 0.145 3.4 08/07/09 40,612,525.8 280.8 1,840.03,001.8 280 60.00 2.955 0.142 3.5 08/07/09 38,472,345.2 278.6 1,840.02,843.6 268 60.00 2.870 0.131 3.1 08/07/09 39,339,132.0 278.6 1,840.02,950.4 275 60.00 2.912 0.137 3.1 08/07/09 39,050,945.9 278.6 1,840.02,907.6 271 60.00 2.598 0.121 1.6 08/07/09 39,464,219.7 280.1 1,840.02,916.9 274 60.00 2.617 0.122 1.6 08/07/09 40,939,204.6 280.6 1,840.03,048.2 285 60.00 1.341 0.065 1.6 08/07/09 39,140,437.9 278.6 1,840.02,914.2 271 60.00 1.341 0.062 1.6 08/07/09 38,388,254.6 275.8 1,840.02,858.2 264 60.00 1.341 0.061 1.6 08/07/09 37,280,846.5 271.51,840.02,735.3 245 60.00 1.361 0.060 0.0 08/07/09 28,758,061.1 265.51,840.02,047.4 180 60.00 1.402 0.046 0.0 08/07/09 27,732,549.0 266.1 1,840.0 1,944.3 173 60.00 0.000 0.000 0.0 08/07/09 26,161,558.8 264.3 1,840.0 1,791.5 158 60.00 0.000 0.000 0.0 08/07/09 24,876,112.1 263.1 1,840.0 1,703.5 152 60.00 0.000 0.000 0.0 08/07/09 24,659,176.0 263.8 1,840.0 1,702.0 153 60.00 0.000 0.000 0.0 08/07/09 26,456,675.4 265.4 1,840.0 1,869.2 169 60.00 0.000 0.000 0.7 08/06/09 27,239,143.2 268.3 1,840.0 1,924.5 178 60.00 0.000 0.000 2.2 08/06/09 30,799,845.7 269.9 1,840.02,243.0 204 60.00 0.600 0.022 2.2 08/06/09 35,064,595.0 274.3 1,840.02,515.5 239 60.00 1.914 0.077 2.5 08/06/09 37,136,684.7 277.2 1,840.02,704.5 256 60.00 1.885 0.082 2.7 08/06/09 39,859,829.7 280.6 1,840.02,924.5 279 60.00 2.126 0.099 3.0 08/06/09 39,694,442.6 281.0 1,840.02,933.9 278 60.00 2.279 0.107 3.0 08/06/09 41,027,761.6 282.7 1,840.03,032.5 289 60.00 2.533 0.123 3.1 08/06/09 40,743,357.6 280.6 1,840.02,989.3 285 60.00 2.551 0.122 2.7 08/06/09 40,765,998.6 279.7 1,840.02,991.0 283 60.00 2.637 0.126 2.6 08/06/09 40,410,895.9 280.51,840.02,986.9 283 60.00 2.279 0.109 2.6 08/06/09 40,491,829.9 281.0 1,840.02,970.9 283 60.00 2.211 0.105 2.5 08/06/09 40,800,941.1 280.4 1,840.02,993.6 283 60.00 2.211 0.106 2.7 08/06/09 40,397,164.2 280.2 1,840.02,985.9 281 60.00 2.111 0.101 2.7 08/06/09 40,206,535.3 280.51,840.02,950.0 278 60.00 2.296 0.108 08/06/09 41,165,273.3 281.8 1,840.03,020.3 282 60.00 2.296 0.111

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 3.5 3.3 08/09/09 42,248,481.7 285.3 1,840.03,007.9 285 60.00 3.068 0.148 3.1 08/09/09 41,765,390.3 283.9 1,840.02,973.5 282 60.00 2.892 0.138 3.2 08/09/09 41,131,132.1 281.8 1,840.02,928.3 275 60.00 2.717 0.127 2.5 08/09/09 41,689,801.8 281.1 1,840.02,945.5 277 60.00 2.826 0.133 2.5 08/09/09 37,169,080.3 270.9 1,840.02,565.5 232 60.00 2.260 0.093 1.9 08/09/09 27,646,834.0 263.6 1,840.0 1,833.1 169 60.00 2.353 0.069 1.9 08/09/09 25,941,748.3 262.2 1,840.0 1,720.1 156 60.00 1.788 0.049 2.1 08/09/09 25,718,415.3 265.8 1,840.0 1,691.2 161 60.00 1.803 0.049 2.2 08/09/09 31,020,034.9 269.6 1,840.02,107.3 197 60.00 1.929 0.065 2.2 08/09/09 30,292,172.7 266.4 1,840.02,041.4 182 60.00 2.037 0.066 2.3 08/09/09 27,753,979.8 266.6 1,840.0 1,840.2 167 60.00 2.070 0.061 2.4 08/08/09 28,706,937.0 269.8 1,840.0 1,981.4 183 60.00 2.079 0.066 2.6 08/08/09 35,009,829.3 275.3 1,840.02,492.6 231 60.00 2.103 0.084 2.8 08/08/09 38,931,208.3 280.0 1,840.02,792.9 266 60.00 2.262 0.101 2.9 08/08/09 40,851,025.9 281.3 1,840.02,975.0 282 60.00 2.399 0.114 2.9 08/08/09 39,977,424.5 282.2 1,840.02,911.4 276 60.00 2.485 0.116 2.7 08/08/09 39,702,886.1 280.7 1,840.02,913.0 274 60.00 2.466 0.115 2.4 08/08/09 41,800,045.8 281.1 1,840.03,021.4 287 60.00 2.331 0.113 2.7 08/08/09 40,533,626.1 280.8 1,840.02,951.9 277 60.00 2.056 0.097 2.8 08/08/09 41,432,753.6 281.9 1,840.03,017.4 284 60.00 2.313 0.112 2.8 08/08/09 41,433,544.3 281.4 1,840.02,995.0 282 60.00 2.417 0.116 3.0 08/08/09 40,528,367.2 279.6 1,840.02,973.5 276 60.00 2.381 0.113 3.0 08/08/09 38,114,545.5 277.0 1,840.02,775.8 260 60.00 2.571 0.114 3.3 08/08/09 39,244,804.8 276.3 1,840.02,858.1 268 60.00 2.571 0.117 2.9 08/08/09 38,090,172.0 273.4 1,840.02,773.9 259 60.00 2.828 0.125 2.7 08/08/09 36,236,496.0 270.51,840.02,599.5 241 60.00 2.522 0.105 2.3 08/08/09 32,447,145.3 268.51,840.02,274.8 214 60.00 2.403 0.087 1.9 08/08/09 33,931,215.8 266.4 1,840.02,434.2 215 60.00 2.001 0.078 1.9 08/08/09 26,286,791.0 260.1 1,840.0 1,814.4 163 60.00 1.718 0.050 1.9 08/08/09 24,572,970.3 259.51,840.0 1,656.0 152 60.00 1.759 0.047 1.9 08/08/09 24,996,693.5 262.3 1,840.0 1,711.8 155 60.00 1.731 0.047 1.9 08/08/09 25,722,417.7 263.7 1,840.0 1,747.4 156 60.00 1.745 0.049 2.1 08/08/09 25,582,752.0 263.4 1,840.0 1,710.2 153 60.00 1.774 0.049 2.5 08/08/09 24,869,491.0 262.3 1,840.0 1,689.5 151 60.00 1.929 0.052 2.8 08/08/09 24,736,342.0 263.2 1,840.0 1,693.9 152 60.00 2.278 0.062 3.1 08/07/09 24,885,894.6 265.1 1,840.0 1,717.7 154 60.00 2.531 0.070 08/07/09 27,501,593.8 270.2 1,840.0 1,943.1 177 60.00 2.738 0.085

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 C 13:00 C 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 3.0 2.8 08/10/09 37,693,262.7 277.9 1,840.02,683.6 251 60.00 2.629 0.113 3.1 08/10/09 37,195,075.6 277.0 1,840.02,648.1 248 60.00 2.454 0.104 3.5 08/10/09 39,320,897.7 284.7 1,840.02,799.5 264 60.00 2.717 0.122 3.5 08/10/09 42,009,586.7 289.4 1,840.03,013.8 285 60.00 3.044 0.147 3.5 08/10/09 42,355,575.1 285.7 1,840.03,038.6 287 60.00 3.044 0.148 3.4 08/10/09 41,756,803.7 282.6 1,840.03,018.3 287 60.00 3.021 0.146 3.4 08/10/09 41,697,368.0 281.4 1,840.03,014.0 286 60.00 2.935 0.141 3.6 08/10/09 41,826,555.0 282.1 1,840.02,977.9 284 60.00 2.980 0.142 3.4 08/10/09 42,381,003.5 283.2 1,840.02,994.3 284 60.00 3.180 0.152 3.1 08/10/09 42,198,661.7 284.4 1,840.03,004.4 284 60.00 2.980 0.143 3.0 08/10/09 41,717,513.1 284.3 1,840.03,038.2 288 60.00 2.656 0.129 3.0 08/10/09 42,313,280.3 282.9 1,840.03,081.5 292 60.00 2.571 0.127 3.2 08/10/09 41,799,607.4 282.4 1,840.03,066.8 292 60.00 2.551 0.125 3.1 08/10/09 41,767,671.1 283.9 1,840.03,064.5 291 60.00 2.722 0.133 2.7 08/10/09 42,244,495.5 283.51,840.03,099.4 292 60.00 2.637 0.131 2.6 08/10/09 40,914,313.6 280.3 1,840.02,935.1 275 60.00 2.349 0.110 2.4 08/10/09 38,823,039.4 279.0 1,840.02,806.2 261 60.00 2.245 0.101 2.6 08/10/09 38,131,826.8 276.2 1,840.02,735.6 253 60.00 2.088 0.091 2.3 08/10/09 36,748,649.1 277.2 1,840.02,636.3 243 60.00 2.262 0.095 2.2 08/10/09 37,183,855.9 275.9 1,840.02,667.5 244 60.00 2.001 0.085 2.2 08/10/09 33,504,859.7 270.9 1,840.02,349.0 208 60.00 1.958 0.074 2.2 08/10/09 28,946,040.2 269.4 1,840.02,013.6 180 60.00 1.973 0.064 2.2 08/10/09 29,549,016.9 268.2 1,840.02,071.6 183 60.00 1.958 0.065 2.6 08/10/09 27,274,951.0 270.51,840.0 1,897.4 175 60.00 1.973 0.060 2.8 08/09/09 34,564,111.0 277.1 1,840.02,460.8 231 60.00 2.279 0.090 2.6 08/09/09 39,062,034.3 279.0 1,840.02,823.5 264 60.00 2.417 0.109 2.8 08/09/09 37,993,570.1 278.1 1,840.02,746.3 255 60.00 2.245 0.099 2.8 08/09/09 39,998,798.8 281.1 1,840.02,891.2 270 60.00 2.417 0.112 2.4 08/09/09 39,302,741.1 278.3 1,840.02,819.6 259 60.00 2.435 0.110 3.2 08/09/09 33,430,337.2 275.0 1,840.02,361.9 218 60.00 2.120 0.080 3.1 08/09/09 37,225,346.6 279.7 1,840.02,670.5 250 60.00 2.783 0.119 2.9 08/09/09 38,048,554.2 277.6 1,840.02,708.9 252 60.00 2.717 0.118 2.9 08/09/09 35,428,117.1 275.6 1,840.02,503.1 233 60.00 2.561 0.103 3.2 08/09/09 37,703,706.4 280.2 1,840.02,622.9 246 60.00 2.601 0.109 3.1 08/09/09 39,213,249.6 283.51,840.02,749.2 259 60.00 2.848 0.125 3.4 08/09/09 40,923,229.6 284.2 1,840.02,891.3 272 60.00 2.738 0.127 08/09/09 39,445,173.4 285.0 1,840.02,786.9 264 60.00 3.003 0.134

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 4.8 5.1 08/12/09 43,020,683.8 284.4 1,840.03,062.9 292 60.00 4.207 0.206 4.7 08/12/09 42,862,768.2 284.6 1,840.03,075.0 292 60.00 4.436 0.218 4.7 08/12/09 42,688,482.1 283.6 1,840.03,085.6 290 60.00 4.057 0.200 4.8 08/12/09 42,270,857.9 280.6 1,840.03,032.5 285 60.00 4.088 0.198 4.4 08/12/09 40,256,608.0 279.1 1,840.02,866.1 267 60.00 4.207 0.193 4.7 08/12/09 36,631,026.4 273.8 1,840.02,568.2 235 60.00 3.916 0.161 3.9 08/12/09 35,212,025.8 271.6 1,840.02,449.5 224 60.00 4.216 0.165 4.1 08/12/09 29,531,423.6 267.1 1,840.02,038.3 179 60.00 3.526 0.115 3.8 08/12/09 29,084,513.2 268.1 1,840.02,039.1 186 60.00 3.649 0.119 3.7 08/12/09 29,930,526.0 267.0 1,840.02,114.7 186 60.00 3.356 0.113 3.7 08/12/09 26,644,384.2 266.6 1,840.0 1,810.1 163 60.00 3.399 0.098 3.9 08/12/09 27,412,781.4 266.7 1,840.0 1,892.1 166 60.00 3.345 0.101 4.3 08/12/09 26,539,340.1 268.51,840.0 1,846.2 166 60.00 3.498 0.103 4.6 08/11/09 29,948,632.0 272.4 1,840.02,099.7 192 60.00 3.827 0.128 4.6 08/11/09 33,706,420.1 277.0 1,840.02,381.4 221 60.00 4.063 0.155 4.5 08/11/09 38,573,632.0 282.7 1,840.02,788.2 261 60.00 3.971 0.177 3.4 08/11/09 40,427,889.3 285.1 1,840.02,966.2 279 60.00 3.827 0.182 3.4 08/11/09 40,841,211.7 284.7 1,840.02,996.5 282 60.00 2.892 0.139 3.5 08/11/09 40,433,444.9 283.7 1,840.02,966.6 278 60.00 2.892 0.137 3.4 08/11/09 41,777,300.2 285.2 1,840.03,065.2 289 60.00 2.977 0.146 3.5 08/11/09 42,014,591.0 284.6 1,840.03,082.6 291 60.00 2.892 0.143 3.2 08/11/09 42,499,433.1 284.9 1,840.03,118.1 291 60.00 2.977 0.148 3.1 08/11/09 42,425,730.6 284.4 1,840.03,089.7 292 60.00 2.742 0.135 3.4 08/11/09 42,482,954.2 284.4 1,840.03,117.0 292 60.00 2.637 0.131 3.0 08/11/09 42,036,796.6 283.8 1,840.03,084.2 290 60.00 2.892 0.143 3.0 08/11/09 42,383,665.0 284.6 1,840.03,109.7 292 60.00 2.551 0.127 3.2 08/11/09 42,309,114.7 283.6 1,840.03,081.2 290 60.00 2.571 0.127 3.0 08/11/09 42,452,906.6 282.6 1,840.03,045.5 289 60.00 2.783 0.136 3.1 08/11/09 42,124,399.6 282.7 1,840.03,044.8 285 60.00 2.590 0.126 3.2 08/11/09 41,696,924.2 282.3 1,840.03,014.0 283 60.00 2.676 0.129 2.9 08/11/09 41,751,485.8 281.1 1,840.02,995.2 281 60.00 2.783 0.133 3.0 08/11/09 37,597,670.7 275.7 1,840.02,635.9 244 60.00 2.581 0.109 2.5 08/11/09 35,886,688.0 273.3 1,840.02,535.5 232 60.00 2.650 0.107 2.7 08/11/09 29,392,562.0 266.51,840.02,060.7 182 60.00 2.225 0.073 2.7 08/11/09 28,183,685.5 270.0 1,840.0 1,960.6 181 60.00 2.422 0.076 2.7 08/11/09 31,668,023.7 273.7 1,840.02,185.8 203 60.00 2.441 0.085 08/11/09 36,844,473.7 278.0 1,840.02,603.1 242 60.00 2.385 0.099

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 2.6 2.7 08/14/09 26,426,194.8 264.6 1,840.0 1,737.8 163 60.00 2.467 0.069 3.1 08/14/09 27,906,803.9 268.8 1,840.0 1,895.9 177 60.00 2.480 0.075 3.1 08/13/09 33,996,352.2 273.6 1,840.02,364.9 222 60.00 2.781 0.105 3.3 08/13/09 36,091,836.9 273.6 1,840.02,569.6 239 60.00 2.717 0.112 3.3 08/13/09 38,439,807.1 277.9 1,840.02,757.7 259 60.00 2.870 0.127 3.4 08/13/09 40,650,482.9 280.4 1,840.02,960.4 278 60.00 2.828 0.134 3.4 08/13/09 41,072,713.8 279.8 1,840.02,991.2 281 60.00 2.913 0.139 3.7 08/13/09 40,811,581.3 278.8 1,840.02,972.2 279 60.00 2.913 0.138 3.6 08/13/09 40,920,553.1 279.3 1,840.02,935.6 279 60.00 3.218 0.151 3.7 08/13/09 41,353,901.5 280.4 1,840.03,011.7 282 60.00 3.085 0.149 3.7 08/13/09 41,446,097.2 281.51,840.03,018.4 281 60.00 3.170 0.153 3.9 08/13/09 41,267,553.1 282.0 1,840.03,005.4 282 60.00 3.170 0.152 3.9 08/13/09 41,483,714.9 282.3 1,840.02,998.6 283 60.00 3.367 0.161 4.0 08/13/09 41,025,963.6 281.7 1,840.02,965.5 281 60.00 3.367 0.160 3.9 08/13/09 41,173,009.9 281.7 1,840.02,976.1 280 60.00 3.453 0.164 3.8 08/13/09 41,239,131.0 280.0 1,840.03,003.3 283 60.00 3.342 0.160 3.8 08/13/09 41,342,181.7 278.7 1,840.03,010.8 283 60.00 3.256 0.157 3.8 08/13/09 39,840,152.4 277.2 1,840.02,858.1 270 60.00 3.305 0.151 3.8 08/13/09 39,798,085.4 276.1 1,840.02,876.7 266 60.00 3.280 0.151 3.3 08/13/09 38,035,587.0 272.0 1,840.02,687.3 250 60.00 3.356 0.144 4.0 08/13/09 31,551,941.8 267.7 1,840.02,229.2 205 60.00 2.915 0.104 3.6 08/13/09 33,041,483.0 266.3 1,840.02,244.6 210 60.00 3.674 0.132 3.3 08/13/09 28,260,301.5 261.4 1,840.0 1,843.0 168 60.00 3.444 0.102 3.1 08/13/09 26,116,825.2 262.2 1,840.0 1,646.5 154 60.00 3.266 0.086 3.1 08/13/09 26,352,933.0 263.51,840.0 1,704.4 154 60.00 2.991 0.082 2.9 08/13/09 27,106,489.9 264.7 1,840.0 1,782.5 160 60.00 2.942 0.084 3.5 08/12/09 26,067,913.5 267.1 1,840.0 1,742.6 158 60.00 2.707 0.075 3.8 08/12/09 33,189,829.5 274.4 1,840.02,326.9 221 60.00 3.115 0.116 3.7 08/12/09 39,438,256.4 278.6 1,840.02,829.2 267 60.00 3.305 0.150 3.6 08/12/09 39,394,010.8 278.8 1,840.02,826.1 265 60.00 3.218 0.145 4.0 08/12/09 41,372,061.4 280.8 1,840.02,990.5 283 60.00 3.108 0.149 4.4 08/12/09 40,684,805.3 279.6 1,840.02,962.9 277 60.00 3.427 0.162 4.6 08/12/09 41,147,637.2 280.3 1,840.02,951.9 280 60.00 3.827 0.181 4.7 08/12/09 41,930,932.2 281.0 1,840.02,962.5 283 60.00 4.063 0.192 4.8 08/12/09 42,932,190.6 284.6 1,840.03,033.2 286 60.00 4.151 0.201 4.6 08/12/09 43,020,620.6 284.8 1,840.03,062.9 290 60.00 4.207 0.206 08/12/09 43,109,792.8 284.9 1,840.03,069.2 291 60.00 4.032 0.198

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 2.7 3.0 08/15/09 40,950,140.9 281.4 1,840.02,982.2 278 60.00 2.313 0.110 3.2 08/15/09 39,965,864.6 281.8 1,840.02,932.3 274 60.00 2.551 0.120 3.2 08/15/09 39,875,813.3 283.4 1,840.02,925.7 273 60.00 2.722 0.127 2.9 08/15/09 40,836,755.5 281.8 1,840.03,018.4 282 60.00 2.702 0.130 3.0 08/15/09 40,386,760.1 279.51,840.02,985.1 279 60.00 2.448 0.117 3.3 08/15/09 40,411,934.5 280.2 1,840.02,987.0 278 60.00 2.533 0.121 3.0 08/15/09 39,797,982.5 278.6 1,840.02,920.0 271 60.00 2.807 0.131 2.3 08/15/09 40,407,633.5 276.6 1,840.02,876.9 263 60.00 2.629 0.121 2.6 08/15/09 29,542,759.8 264.51,840.02,055.2 183 60.00 2.063 0.068 2.8 08/15/09 25,224,299.8 263.8 1,840.0 1,699.9 154 60.00 2.407 0.065 2.9 08/15/09 27,036,281.8 265.4 1,840.0 1,880.8 169 60.00 2.512 0.076 2.7 08/15/09 26,432,239.4 265.51,840.0 1,838.7 166 60.00 2.601 0.076 2.9 08/15/09 27,921,605.2 268.6 1,840.0 1,957.6 177 60.00 2.403 0.075 2.9 08/15/09 29,500,843.3 269.7 1,840.02,068.3 188 60.00 2.581 0.085 3.0 08/15/09 32,220,107.8 272.2 1,840.02,241.4 209 60.00 2.601 0.093 2.5 08/14/09 36,115,291.9 273.9 1,840.02,492.7 239 60.00 2.712 0.108 3.0 08/14/09 36,508,199.2 275.4 1,840.02,559.5 243 60.00 2.225 0.091 3.0 08/14/09 39,774,452.7 279.9 1,840.02,896.6 271 60.00 2.571 0.119 3.3 08/14/09 40,236,831.5 282.0 1,840.02,974.0 276 60.00 2.533 0.120 3.2 08/14/09 41,216,240.9 281.8 1,840.03,024.0 282 60.00 2.807 0.136 3.2 08/14/09 41,129,963.2 281.7 1,840.02,973.0 280 60.00 2.762 0.131 3.2 08/14/09 41,228,475.4 282.0 1,840.02,980.1 282 60.00 2.762 0.132 3.2 08/14/09 41,451,260.4 281.4 1,840.02,996.2 282 60.00 2.762 0.132 3.2 08/14/09 41,372,574.5 280.7 1,840.02,990.5 282 60.00 2.762 0.132 3.6 08/14/09 41,504,662.2 281.3 1,840.03,000.1 282 60.00 2.762 0.133 3.8 08/14/09 41,639,100.8 282.1 1,840.03,009.8 282 60.00 3.108 0.150 3.6 08/14/09 41,755,018.4 282.2 1,840.03,018.2 282 60.00 3.280 0.158 3.4 08/14/09 41,470,645.4 280.7 1,840.02,997.6 282 60.00 3.108 0.149 3.5 08/14/09 41,230,265.9 279.7 1,840.02,980.2 282 60.00 2.935 0.140 3.7 08/14/09 41,350,950.9 280.1 1,840.03,011.4 282 60.00 2.999 0.144 3.8 08/14/09 41,474,082.4 279.51,840.02,975.3 281 60.00 3.218 0.153 3.4 08/14/09 41,618,146.2 278.4 1,840.03,008.3 281 60.00 3.280 0.158 3.0 08/14/09 37,645,714.6 271.0 1,840.02,721.2 249 60.00 2.935 0.128 3.3 08/14/09 31,127,915.9 268.1 1,840.02,182.3 202 60.00 2.670 0.093 2.9 08/14/09 32,172,680.9 268.51,840.02,255.6 209 60.00 2.937 0.106 2.7 08/14/09 29,142,113.2 264.9 1,840.02,011.4 183 60.00 2.622 0.084 08/14/09 27,311,892.2 263.6 1,840.0 1,781.2 175 60.00 2.583 0.074

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 2.4 2.5 08/17/09 27,447,490.0 264.4 1,840.0 1,819.9 163 60.00 2.259 0.066 2.7 08/17/09 25,900,771.5 263.4 1,840.0 1,703.3 154 60.00 2.372 0.065 2.7 08/17/09 24,897,807.7 263.4 1,840.0 1,664.4 151 60.00 2.520 0.067 2.9 08/17/09 26,061,356.3 265.4 1,840.0 1,713.8 157 60.00 2.562 0.070 3.4 08/16/09 28,153,049.7 269.8 1,840.0 1,851.4 173 60.00 2.752 0.081 3.7 08/16/09 34,005,842.1 277.6 1,840.02,310.2 221 60.00 3.123 0.115 3.7 08/16/09 41,120,376.9 280.8 1,840.02,860.5 273 60.00 3.319 0.152 3.8 08/16/09 40,531,931.5 280.8 1,840.02,819.6 270 60.00 3.319 0.150 3.6 08/16/09 41,757,916.8 283.9 1,840.02,927.6 278 60.00 3.382 0.158 3.8 08/16/09 41,078,066.0 280.3 1,840.02,835.3 273 60.00 3.255 0.148 3.8 08/16/09 40,404,082.4 280.0 1,840.02,788.8 267 60.00 3.435 0.153 3.8 08/16/09 38,024,899.0 277.51,840.02,686.5 251 60.00 3.356 0.144 3.3 08/16/09 37,897,528.8 277.1 1,840.02,698.2 251 60.00 3.331 0.144 3.4 08/16/09 36,956,819.2 276.2 1,840.02,611.1 241 60.00 2.915 0.122 3.6 08/16/09 38,713,013.5 279.6 1,840.02,735.2 257 60.00 3.003 0.131 3.8 08/16/09 40,426,585.2 279.3 1,840.02,878.2 268 60.00 3.155 0.145 3.2 08/16/09 37,696,328.6 275.9 1,840.02,683.8 246 60.00 3.331 0.143 3.2 08/16/09 36,883,364.1 276.0 1,840.02,625.9 244 60.00 2.805 0.118 3.2 08/16/09 40,181,532.3 279.1 1,840.02,904.5 269 60.00 2.762 0.128 3.0 08/16/09 41,376,410.1 279.9 1,840.02,968.3 278 60.00 2.783 0.132 2.5 08/16/09 38,551,433.9 272.3 1,840.02,765.6 249 60.00 2.609 0.115 2.6 08/16/09 29,007,319.6 264.2 1,840.02,033.6 177 60.00 2.225 0.072 2.8 08/16/09 26,881,451.7 266.8 1,840.0 1,840.8 161 60.00 2.369 0.070 2.7 08/16/09 29,094,054.2 267.6 1,840.02,071.4 183 60.00 2.454 0.081 2.5 08/16/09 29,320,814.9 267.2 1,840.02,071.6 183 60.00 2.385 0.079 2.1 08/16/09 28,926,734.7 265.9 1,840.02,012.3 181 60.00 2.242 0.072 2.0 08/16/09 26,796,032.9 264.9 1,840.0 1,864.1 162 60.00 1.884 0.056 2.4 08/16/09 28,605,192.6 267.8 1,840.0 1,989.9 179 60.00 1.794 0.057 3.0 08/15/09 30,270,878.4 270.6 1,840.02,089.4 193 60.00 2.170 0.072 2.9 08/15/09 37,058,368.0 277.0 1,840.02,638.4 246 60.00 2.629 0.111 3.0 08/15/09 39,771,061.5 279.6 1,840.02,896.4 269 60.00 2.485 0.115 2.9 08/15/09 39,336,080.3 280.1 1,840.02,907.4 268 60.00 2.533 0.118 2.6 08/15/09 39,844,608.7 280.2 1,840.02,945.1 272 60.00 2.448 0.115 2.4 08/15/09 39,929,936.4 279.9 1,840.02,864.5 267 60.00 2.262 0.104 2.3 08/15/09 39,618,749.2 280.8 1,840.02,863.8 268 60.00 2.072 0.095 2.5 08/15/09 40,724,496.1 282.0 1,840.02,965.8 280 60.00 1.971 0.093 08/15/09 40,214,944.1 280.6 1,840.02,928.7 275 60.00 2.142 0.100

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 5.6 5.6 08/18/09 41,822,731.3 285.0 1,840.02,977.6 282 60.00 4.908 0.234 5.7 08/18/09 41,644,620.2 285.0 1,840.02,964.9 281 60.00 4.908 0.233 5.5 08/18/09 41,670,613.7 284.6 1,840.02,989.4 282 60.00 4.958 0.237 5.4 08/18/09 41,608,103.5 285.8 1,840.02,984.9 282 60.00 4.784 0.228 5.3 08/18/09 41,644,324.0 286.2 1,840.03,032.8 282 60.00 4.627 0.224 5.3 08/18/09 41,158,046.5 287.8 1,840.02,997.4 279 60.00 4.541 0.218 5.6 08/18/09 41,212,120.5 286.7 1,840.03,001.3 279 60.00 4.541 0.218 5.5 08/18/09 41,193,313.2 285.6 1,840.02,999.9 280 60.00 4.798 0.230 5.2 08/18/09 41,051,973.9 282.51,840.02,989.7 277 60.00 4.713 0.225 4.4 08/18/09 39,399,575.5 277.2 1,840.02,826.5 260 60.00 4.523 0.204 4.1 08/18/09 32,210,622.9 267.7 1,840.02,153.2 195 60.00 4.107 0.141 4.2 08/18/09 27,151,791.8 267.7 1,840.0 1,770.8 164 60.00 3.923 0.111 4.0 08/18/09 29,857,944.7 267.51,840.0 1,947.3 180 60.00 4.019 0.125 4.2 08/18/09 27,824,716.8 265.7 1,840.0 1,799.6 166 60.00 3.859 0.111 4.1 08/18/09 27,446,214.5 265.51,840.0 1,745.2 159 60.00 4.122 0.115 4.0 08/18/09 26,997,436.8 265.0 1,840.0 1,746.0 159 60.00 3.956 0.110 4.7 08/18/09 25,903,191.8 267.3 1,840.0 1,689.3 157 60.00 3.827 0.103 4.8 08/17/09 30,139,259.6 269.7 1,840.0 1,965.6 184 60.00 4.497 0.141 4.9 08/17/09 32,109,060.7 272.1 1,840.02,146.4 201 60.00 4.481 0.154 4.9 08/17/09 33,943,704.4 274.0 1,840.02,287.5 217 60.00 4.537 0.166 4.9 08/17/09 35,176,588.5 276.0 1,840.02,370.6 225 60.00 4.537 0.172 5.1 08/17/09 40,740,154.7 282.4 1,840.02,811.9 271 60.00 4.430 0.199 5.0 08/17/09 42,434,667.6 283.3 1,840.02,952.0 281 60.00 4.575 0.216 5.0 08/17/09 40,447,235.6 280.7 1,840.02,791.7 262 60.00 4.520 0.202 5.1 08/17/09 39,217,616.9 281.7 1,840.02,728.2 259 60.00 4.485 0.196 5.1 08/17/09 41,924,978.0 282.4 1,840.02,939.3 280 60.00 4.539 0.213 4.9 08/17/09 42,066,463.7 283.3 1,840.02,949.2 279 60.00 4.539 0.214 4.8 08/17/09 41,311,514.7 283.3 1,840.02,896.3 275 60.00 4.361 0.202 5.1 08/17/09 42,321,253.0 284.2 1,840.02,967.1 282 60.00 4.272 0.203 5.0 08/17/09 40,857,524.6 283.6 1,840.02,886.7 273 60.00 4.504 0.208 5.1 08/17/09 41,090,104.8 282.7 1,840.02,925.4 276 60.00 4.382 0.205 4.8 08/17/09 41,702,821.1 282.7 1,840.02,991.7 282 60.00 4.436 0.212 4.3 08/17/09 41,051,552.0 281.51,840.02,967.3 277 60.00 4.144 0.197 3.9 08/17/09 38,868,013.3 279.0 1,840.02,788.4 258 60.00 3.740 0.167 3.2 08/17/09 40,682,519.0 279.7 1,840.02,918.6 272 60.00 3.392 0.158 2.5 08/17/09 38,025,111.4 272.9 1,840.02,665.9 244 60.00 2.848 0.121 08/17/09 31,632,899.0 267.6 1,840.02,149.0 196 60.00 2.296 0.079

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 * * 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 4.2 3.8 08/20/09 31,266,961.6 267.1 1,840.02,124.1 190 60.00 3.858 0.131 3.3 08/20/09 27,646,922.0 267.3 1,840.0 1,788.0 166 60.00 3.666 0.105 3.4 08/20/09 29,269,525.4 267.0 1,840.0 1,908.9 173 60.00 3.157 0.096 3.4 08/20/09 26,999,789.6 266.9 1,840.0 1,672.8 155 60.00 3.424 0.092 3.7 08/20/09 29,105,770.3 267.1 1,840.0 1,850.8 169 60.00 3.337 0.099 3.7 08/20/09 27,190,511.7 268.6 1,840.0 1,699.4 163 60.00 3.694 0.100 3.6 08/19/09 29,824,269.0 267.6 1,840.0 1,880.2 178 60.00 3.662 0.110 4.4 08/19/09 28,901,919.7 272.0 1,840.0 1,822.1 175 60.00 3.563 0.104 5.0 08/19/09 34,478,093.1 278.9 1,840.02,323.5 221 60.00 4.074 0.151 5.1 08/19/09 40,454,223.7 283.51,840.02,792.2 268 60.00 4.520 0.202 5.6 08/19/09 40,704,024.5 286.2 1,840.02,809.5 268 60.00 4.611 0.207 5.8 08/19/09 41,835,352.5 286.0 1,840.02,933.0 280 60.00 4.984 0.234 5.7 08/19/09 40,946,324.1 284.2 1,840.02,848.4 272 60.00 5.203 0.237 5.6 08/19/09 41,695,307.5 284.1 1,840.02,900.5 278 60.00 5.113 0.237 5.7 08/19/09 40,900,767.6 283.3 1,840.02,889.7 274 60.00 4.946 0.229 5.7 08/19/09 40,817,414.8 284.3 1,840.02,839.4 272 60.00 5.113 0.232 5.7 08/19/09 41,592,416.3 285.3 1,840.02,893.4 277 60.00 5.113 0.237 6.6 08/19/09 39,970,500.0 289.9 1,840.02,780.6 265 60.00 5.113 0.227 6.0 08/19/09 41,592,778.5 300.0 1,840.02,983.8 279 60.00 5.741 0.274 5.2 08/19/09 41,165,629.2 287.51,840.02,953.2 275 60.00 5.219 0.246 5.3 08/19/09 37,892,898.5 279.6 1,840.02,697.8 251 60.00 4.558 0.197 5.3 08/19/09 40,198,761.8 282.51,840.02,883.8 267 60.00 4.610 0.213 4.5 08/19/09 39,536,562.7 280.2 1,840.02,814.9 260 60.00 4.645 0.209 4.4 08/19/09 37,915,919.9 273.7 1,840.02,637.6 241 60.00 4.037 0.170 4.5 08/19/09 28,884,942.2 269.8 1,840.0 1,962.3 181 60.00 4.042 0.127 4.4 08/19/09 29,921,425.8 268.4 1,840.02,000.2 186 60.00 4.201 0.134 3.9 08/19/09 30,622,798.6 268.7 1,840.02,047.1 190 60.00 4.107 0.134 4.3 08/19/09 27,477,951.1 266.1 1,840.0 1,807.0 164 60.00 3.701 0.107 4.3 08/19/09 26,334,842.1 266.51,840.0 1,731.8 157 60.00 4.080 0.113 4.7 08/19/09 26,165,810.0 268.3 1,840.0 1,706.5 160 60.00 4.114 0.112 4.2 08/18/09 30,782,492.4 268.9 1,840.02,057.7 191 60.00 4.387 0.144 4.6 08/18/09 26,303,761.0 268.2 1,840.0 1,715.5 161 60.00 4.019 0.110 5.3 08/18/09 30,726,984.5 276.4 1,840.02,054.0 198 60.00 4.294 0.141 5.3 08/18/09 39,188,119.2 282.0 1,840.02,768.7 260 60.00 4.681 0.207 5.3 08/18/09 39,991,391.6 283.2 1,840.02,847.2 267 60.00 4.645 0.211 5.5 08/18/09 40,404,747.6 282.8 1,840.02,876.7 271 60.00 4.645 0.214 08/18/09 41,865,690.4 285.4 1,840.02,980.7 282 60.00 4.821 0.230

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 4.0 3.8 08/21/09 31,830,245.5 265.0 1,840.02,127.8 198 60.00 3.734 0.127 4.0 08/21/09 27,711,191.3 266.7 1,840.0 1,822.3 169 60.00 3.606 0.105 3.9 08/21/09 32,267,015.8 269.0 1,840.02,192.1 201 60.00 3.674 0.129 4.3 08/21/09 32,142,384.5 271.0 1,840.02,218.5 206 60.00 3.526 0.125 4.7 08/21/09 36,631,236.3 273.4 1,840.02,588.1 241 60.00 3.798 0.157 5.1 08/21/09 38,341,064.2 276.4 1,840.02,708.9 254 60.00 4.151 0.180 4.9 08/21/09 40,112,066.5 277.7 1,840.02,812.2 265 60.00 4.539 0.204 4.6 08/21/09 38,709,864.4 273.51,840.02,650.8 247 60.00 4.465 0.189 4.0 08/21/09 36,745,717.9 272.6 1,840.02,476.4 234 60.00 4.259 0.169 3.9 08/21/09 33,996,807.1 269.6 1,840.02,291.1 212 60.00 3.704 0.136 3.5 08/21/09 32,859,709.4 269.6 1,840.02,196.6 204 60.00 3.641 0.128 4.2 08/21/09 29,850,418.0 265.4 1,840.0 1,979.2 177 60.00 3.294 0.104 4.2 08/21/09 30,453,269.1 267.51,840.02,035.7 193 60.00 3.921 0.128 3.4 08/21/09 33,134,366.6 266.1 1,840.02,269.0 209 60.00 3.827 0.139 3.2 08/21/09 28,257,161.4 262.9 1,840.0 1,904.3 173 60.00 3.148 0.096 3.1 08/21/09 26,548,233.2 264.1 1,840.0 1,745.8 160 60.00 3.036 0.085 3.5 08/21/09 26,421,679.5 264.1 1,840.0 1,708.8 156 60.00 2.991 0.082 3.5 08/21/09 26,426,743.0 264.0 1,840.0 1,723.5 154 60.00 3.349 0.092 3.8 08/21/09 25,823,095.9 263.7 1,840.0 1,698.1 154 60.00 3.321 0.090 3.6 08/20/09 27,719,128.5 264.51,840.0 1,837.9 169 60.00 3.576 0.105 3.7 08/20/09 27,393,996.1 264.7 1,840.0 1,801.5 166 60.00 3.416 0.098 4.5 08/20/09 27,576,000.6 267.2 1,840.0 1,798.4 166 60.00 3.540 0.102 4.9 08/20/09 31,935,748.9 271.0 1,840.02,100.1 197 60.00 4.270 0.143 4.9 08/20/09 36,832,822.1 274.0 1,840.02,502.2 237 60.00 4.501 0.180 5.2 08/20/09 37,504,741.1 273.1 1,840.02,547.9 243 60.00 4.501 0.183 5.5 08/20/09 39,351,263.2 275.2 1,840.02,694.7 263 60.00 4.738 0.204 6.1 08/20/09 39,873,611.3 274.7 1,840.02,687.2 264 60.00 5.093 0.219 6.3 08/20/09 38,568,170.7 270.2 1,840.02,557.2 246 60.00 5.741 0.235 5.0 08/20/09 35,895,896.4 269.8 1,840.02,360.6 229 60.00 5.978 0.226 4.3 08/20/09 32,703,684.7 264.0 1,840.02,150.6 200 60.00 4.744 0.163 4.3 08/20/09 26,633,574.8 261.9 1,840.0 1,693.6 157 60.00 4.220 0.114 4.5 08/20/09 26,786,971.8 263.4 1,840.0 1,688.7 157 60.00 4.256 0.115 3.6 08/20/09 27,767,293.7 266.2 1,840.0 1,765.6 164 60.00 4.416 0.125 3.6 08/20/09 29,628,614.0 266.9 1,840.0 1,900.1 174 60.00 3.503 0.106 4.3 08/20/09 26,783,029.8 266.2 1,840.0 1,673.9 157 60.00 3.594 0.096 4.3 08/20/09 29,220,390.2 270.0 1,840.0 1,858.0 177 60.00 4.220 0.125 08/20/09 30,081,717.8 269.3 1,840.0 1,978.2 182 60.00 4.080 0.129

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 4.1 4.5 08/23/09 27,476,042.0 265.3 1,840.0 1,881.5 167 60.00 3.736 0.112 4.4 08/23/09 27,265,380.2 263.2 1,840.0 1,896.7 165 60.00 4.037 0.122 4.3 08/23/09 25,425,577.2 262.3 1,840.0 1,741.1 154 60.00 4.009 0.112 4.1 08/23/09 25,211,250.1 262.4 1,840.0 1,726.4 153 60.00 3.918 0.108 4.1 08/23/09 25,860,110.1 263.7 1,840.0 1,756.8 155 60.00 3.766 0.106 4.3 08/23/09 25,771,477.4 263.7 1,840.0 1,736.7 154 60.00 3.796 0.105 4.3 08/23/09 26,175,995.1 264.0 1,840.0 1,778.3 156 60.00 3.950 0.112 4.4 08/23/09 25,849,531.0 262.9 1,840.0 1,756.1 155 60.00 3.950 0.111 4.2 08/22/09 25,270,913.3 262.9 1,840.0 1,744.2 154 60.00 3.978 0.111 4.6 08/22/09 25,268,496.6 264.51,840.0 1,744.0 155 60.00 3.797 0.106 4.7 08/22/09 28,884,201.5 266.8 1,840.0 1,962.2 181 60.00 4.225 0.133 5.1 08/22/09 31,025,558.5 269.7 1,840.02,107.7 199 60.00 4.317 0.146 5.0 08/22/09 36,162,194.9 274.8 1,840.02,476.3 233 60.00 4.647 0.184 4.8 08/22/09 35,393,062.1 270.3 1,840.02,442.9 222 60.00 4.520 0.177 4.9 08/22/09 31,583,492.3 268.0 1,840.02,128.4 197 60.00 4.444 0.151 5.2 08/22/09 31,486,430.6 270.6 1,840.02,173.2 203 60.00 4.430 0.154 4.8 08/22/09 34,962,440.7 270.7 1,840.02,394.1 221 60.00 4.738 0.181 4.8 08/22/09 32,519,897.0 269.8 1,840.02,138.5 203 60.00 4.555 0.156 4.5 08/22/09 33,540,423.2 269.4 1,840.02,315.0 214 60.00 4.340 0.161 4.3 08/22/09 31,359,636.6 267.8 1,840.02,147.5 199 60.00 4.101 0.141 3.9 08/22/09 33,009,216.8 269.0 1,840.02,314.2 214 60.00 3.827 0.142 3.8 08/22/09 33,930,359.8 270.4 1,840.02,415.7 220 60.00 3.418 0.132 4.2 08/22/09 33,762,233.8 271.4 1,840.02,403.7 219 60.00 3.331 0.128 4.6 08/22/09 34,856,584.0 272.3 1,840.02,481.7 225 60.00 3.681 0.146 4.1 08/22/09 36,249,363.1 270.51,840.02,561.1 235 60.00 4.063 0.166 4.0 08/22/09 31,287,849.0 264.51,840.02,176.6 198 60.00 3.678 0.128 3.6 08/22/09 28,175,329.7 264.9 1,840.0 1,898.8 177 60.00 3.704 0.112 3.6 08/22/09 31,929,587.9 266.4 1,840.02,221.2 205 60.00 3.229 0.115 3.6 08/22/09 26,866,479.3 264.0 1,840.0 1,868.9 165 60.00 3.229 0.097 3.5 08/22/09 26,865,657.5 264.51,840.0 1,839.7 169 60.00 3.280 0.097 4.0 08/22/09 25,989,440.6 263.7 1,840.0 1,836.2 158 60.00 3.091 0.091 3.9 08/22/09 27,289,794.4 265.51,840.0 1,898.4 173 60.00 3.588 0.109 3.7 08/21/09 29,363,208.5 265.1 1,840.02,074.6 187 60.00 3.444 0.114 3.9 08/21/09 28,071,874.7 265.3 1,840.0 1,907.1 174 60.00 3.399 0.104 4.1 08/21/09 29,257,184.5 266.3 1,840.0 1,955.8 181 60.00 3.641 0.114 4.4 08/21/09 31,612,189.5 268.0 1,840.02,061.7 198 60.00 3.923 0.129 08/21/09 31,391,376.1 266.1 1,840.02,081.4 198 60.00 4.141 0.138

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 4.1 4.6 08/24/09 36,898,419.2 273.51,840.02,566.8 242 60.00 3.678 0.151 4.8 08/24/09 40,119,430.8 275.4 1,840.02,790.9 268 60.00 4.126 0.184 5.4 08/24/09 39,767,013.2 273.6 1,840.02,809.6 268 60.00 4.239 0.190 5.5 08/24/09 40,821,199.7 273.6 1,840.02,884.1 280 60.00 4.769 0.220 5.7 08/24/09 39,886,186.1 274.2 1,840.02,818.0 271 60.00 4.858 0.219 6.1 08/24/09 41,036,875.7 276.0 1,840.02,921.7 279 60.00 4.996 0.233 6.5 08/24/09 41,062,437.9 275.51,840.02,901.1 278 60.00 5.388 0.250 6.5 08/24/09 40,175,256.5 274.0 1,840.02,838.5 274 60.00 5.741 0.261 6.2 08/24/09 40,618,658.8 275.4 1,840.02,891.9 279 60.00 5.697 0.263 5.7 08/24/09 40,838,426.2 276.4 1,840.02,907.5 280 60.00 5.434 0.253 5.4 08/24/09 39,086,063.9 275.1 1,840.02,782.8 265 60.00 4.996 0.222 5.4 08/24/09 39,456,081.6 277.4 1,840.02,787.7 264 60.00 4.769 0.213 5.2 08/24/09 41,094,651.0 278.1 1,840.02,903.5 274 60.00 4.769 0.221 4.8 08/24/09 40,602,703.7 276.4 1,840.02,890.8 270 60.00 4.558 0.211 4.8 08/24/09 38,618,676.3 274.51,840.02,728.5 253 60.00 4.239 0.185 5.0 08/24/09 36,755,783.6 273.51,840.02,576.9 238 60.00 4.272 0.176 4.6 08/24/09 38,514,136.8 274.3 1,840.02,700.2 251 60.00 4.450 0.192 4.1 08/24/09 33,102,234.6 266.1 1,840.02,248.8 207 60.00 4.225 0.152 4.0 08/24/09 28,584,666.3 263.9 1,840.0 1,910.8 171 60.00 3.827 0.117 4.1 08/24/09 26,966,762.8 263.51,840.0 1,773.4 160 60.00 3.796 0.108 3.9 08/24/09 27,288,765.0 265.0 1,840.0 1,779.7 163 60.00 3.923 0.112 4.0 08/23/09 29,122,963.9 265.4 1,840.0 1,978.5 180 60.00 3.582 0.113 4.1 08/23/09 27,493,928.6 267.3 1,840.0 1,882.7 169 60.00 3.645 0.110 4.4 08/23/09 31,386,429.8 269.9 1,840.02,183.4 197 60.00 3.678 0.128 4.9 08/23/09 32,970,887.3 274.1 1,840.02,311.6 214 60.00 3.916 0.145 4.6 08/23/09 39,291,288.1 277.9 1,840.02,840.1 262 60.00 4.230 0.192 4.7 08/23/09 37,331,883.0 275.1 1,840.02,698.5 244 60.00 3.971 0.171 4.9 08/23/09 36,938,116.9 275.0 1,840.02,649.9 243 60.00 4.088 0.173 4.3 08/23/09 38,686,004.1 275.7 1,840.02,796.3 258 60.00 4.230 0.189 4.3 08/23/09 35,309,099.2 272.51,840.02,571.4 229 60.00 3.684 0.151 4.4 08/23/09 34,481,712.5 271.9 1,840.02,473.7 221 60.00 3.740 0.148 4.5 08/23/09 33,334,150.9 270.6 1,840.02,355.1 211 60.00 3.886 0.146 4.5 08/23/09 32,955,823.1 269.51,840.02,310.5 208 60.00 4.005 0.148 4.3 08/23/09 31,357,957.1 267.0 1,840.02,198.5 198 60.00 4.005 0.141 4.3 08/23/09 31,126,665.5 267.2 1,840.02,165.4 197 60.00 3.857 0.134 4.2 08/23/09 30,563,295.1 267.51,840.02,092.9 190 60.00 3.918 0.131 08/23/09 32,025,809.3 266.4 1,840.02,227.9 196 60.00 3.767 0.134

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 3.4 3.4 08/26/09 33,048,852.7 268.3 1,840.02,281.1 211 60.00 3.074 0.112 3.5 08/26/09 34,040,203.0 267.9 1,840.02,349.5 214 60.00 3.074 0.115 3.1 08/26/09 33,572,463.3 270.6 1,840.02,317.2 217 60.00 3.164 0.117 2.9 08/26/09 36,119,451.1 269.3 1,840.02,532.3 230 60.00 2.759 0.112 2.4 08/26/09 31,954,612.9 264.51,840.02,223.0 202 60.00 2.601 0.092 2.4 08/26/09 28,340,050.2 260.8 1,840.0 1,971.5 176 60.00 2.153 0.068 2.7 08/26/09 25,482,396.7 261.2 1,840.0 1,717.3 155 60.00 2.222 0.061 2.8 08/26/09 26,316,955.7 261.2 1,840.0 1,730.6 158 60.00 2.562 0.071 2.6 08/26/09 26,121,312.4 262.0 1,840.0 1,731.9 156 60.00 2.635 0.073 2.7 08/26/09 26,517,546.4 262.51,840.0 1,772.7 160 60.00 2.427 0.069 2.8 08/25/09 28,531,899.8 265.3 1,840.0 1,922.8 176 60.00 2.500 0.077 3.1 08/25/09 30,276,690.0 267.7 1,840.02,056.9 189 60.00 2.572 0.085 3.6 08/25/09 34,062,935.3 271.0 1,840.02,369.6 222 60.00 2.781 0.105 3.7 08/25/09 37,841,641.2 274.51,840.02,673.6 254 60.00 3.180 0.136 3.9 08/25/09 39,510,858.0 276.1 1,840.02,813.0 266 60.00 3.243 0.146 4.0 08/25/09 40,381,043.8 276.51,840.02,875.0 273 60.00 3.418 0.157 3.8 08/25/09 41,831,663.8 276.6 1,840.02,910.1 278 60.00 3.588 0.167 3.7 08/25/09 41,357,082.4 276.2 1,840.02,854.5 274 60.00 3.435 0.157 3.7 08/25/09 42,298,436.6 277.4 1,840.02,873.5 277 60.00 3.399 0.156 3.8 08/25/09 42,118,274.4 277.51,840.02,861.3 277 60.00 3.399 0.155 3.9 08/25/09 42,397,888.0 277.7 1,840.02,903.3 278 60.00 3.463 0.161 3.8 08/25/09 41,755,102.9 275.9 1,840.02,859.3 275 60.00 3.554 0.162 4.1 08/25/09 42,444,174.5 276.1 1,840.02,906.5 278 60.00 3.463 0.161 4.2 08/25/09 41,217,787.2 275.0 1,840.02,800.1 265 60.00 3.766 0.169 4.0 08/25/09 40,084,701.7 273.1 1,840.02,723.2 256 60.00 3.858 0.168 3.8 08/25/09 37,940,506.2 270.1 1,840.02,577.5 239 60.00 3.674 0.151 3.5 08/25/09 32,984,979.5 266.8 1,840.02,240.8 209 60.00 3.490 0.125 3.2 08/25/09 32,194,759.2 264.0 1,840.02,239.7 200 60.00 3.139 0.112 3.4 08/25/09 28,154,827.5 263.0 1,840.0 1,958.6 174 60.00 2.870 0.090 3.0 08/25/09 27,999,576.3 264.51,840.0 1,917.4 174 60.00 3.098 0.095 3.3 08/25/09 27,662,737.9 263.3 1,840.0 1,894.3 166 60.00 2.734 0.083 3.3 08/25/09 26,199,798.0 261.9 1,840.0 1,794.1 156 60.00 3.007 0.086 3.3 08/25/09 25,474,767.1 261.1 1,840.0 1,730.6 153 60.00 3.031 0.084 3.7 08/25/09 25,475,488.5 262.6 1,840.0 1,702.9 156 60.00 3.080 0.084 3.4 08/24/09 28,735,276.8 265.3 1,840.0 1,920.9 180 60.00 3.454 0.106 3.5 08/24/09 30,011,096.3 266.2 1,840.02,022.5 190 60.00 3.148 0.102 08/24/09 33,724,291.9 270.4 1,840.02,309.4 217 60.00 3.189 0.118

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 3.5 3.6 08/27/09 30,517,947.4 270.9 1,840.02,189.3 204 60.00 3.044 0.107 3.9 08/27/09 38,094,117.3 276.7 1,840.02,753.5 258 60.00 3.108 0.137 3.9 08/27/09 40,128,682.7 279.1 1,840.02,944.2 276 60.00 3.317 0.156 4.3 08/27/09 40,261,399.4 279.2 1,840.02,953.9 276 60.00 3.317 0.157 4.5 08/27/09 40,220,033.3 278.6 1,840.02,972.8 278 60.00 3.630 0.173 4.4 08/27/09 39,778,080.3 278.7 1,840.02,940.1 274 60.00 3.799 0.179 4.4 08/27/09 39,959,981.4 277.9 1,840.02,931.8 276 60.00 3.742 0.175 4.5 08/27/09 39,750,828.9 277.1 1,840.02,916.5 274 60.00 3.742 0.175 4.5 08/27/09 39,237,847.1 277.4 1,840.02,878.9 270 60.00 3.827 0.176 4.5 08/27/09 40,571,963.2 277.8 1,840.02,998.8 281 60.00 3.799 0.182 4.4 08/27/09 41,124,815.6 278.51,840.03,017.3 282 60.00 3.827 0.185 4.3 08/27/09 39,602,537.9 278.0 1,840.02,905.7 270 60.00 3.742 0.174 4.3 08/27/09 40,557,532.9 279.1 1,840.02,975.7 278 60.00 3.657 0.174 4.2 08/27/09 39,632,838.9 277.51,840.02,929.4 273 60.00 3.630 0.170 4.2 08/27/09 39,284,349.8 276.2 1,840.02,882.3 268 60.00 3.572 0.165 4.0 08/27/09 39,795,697.5 275.6 1,840.02,919.8 272 60.00 3.572 0.167 3.6 08/27/09 35,747,477.5 268.51,840.02,622.7 234 60.00 3.402 0.143 3.3 08/27/09 26,802,547.3 262.4 1,840.0 1,937.4 171 60.00 3.108 0.096 3.3 08/27/09 24,641,722.0 262.3 1,840.0 1,754.4 158 60.00 2.892 0.081 3.6 08/27/09 24,734,446.6 263.6 1,840.0 1,720.6 156 60.00 2.960 0.081 3.5 08/27/09 26,179,474.9 263.3 1,840.0 1,778.5 159 60.00 3.307 0.094 3.5 08/27/09 26,033,625.0 263.6 1,840.0 1,768.6 157 60.00 3.215 0.091 3.4 08/27/09 25,985,621.1 262.9 1,840.0 1,807.7 160 60.00 3.139 0.091 3.5 08/26/09 27,201,191.6 264.9 1,840.0 1,892.2 170 60.00 3.050 0.092 4.1 08/26/09 30,403,694.7 271.7 1,840.02,148.1 199 60.00 3.091 0.106 4.4 08/26/09 38,023,226.4 274.8 1,840.02,727.7 253 60.00 3.566 0.156 4.3 08/26/09 37,669,757.4 276.0 1,840.02,702.4 250 60.00 3.827 0.165 4.6 08/26/09 39,694,515.5 277.9 1,840.02,890.8 271 60.00 3.684 0.170 4.8 08/26/09 40,352,779.6 278.51,840.02,960.7 279 60.00 3.912 0.185 4.9 08/26/09 40,871,409.0 278.2 1,840.02,976.5 280 60.00 4.113 0.196 4.9 08/26/09 40,002,344.4 277.2 1,840.02,891.4 272 60.00 4.230 0.196 4.6 08/26/09 40,862,349.9 277.0 1,840.02,975.8 279 60.00 4.198 0.200 4.6 08/26/09 41,293,590.5 276.6 1,840.02,962.4 279 60.00 4.001 0.190 4.1 08/26/09 41,148,792.8 277.0 1,840.02,929.6 276 60.00 4.032 0.189 4.1 08/26/09 40,454,965.4 274.2 1,840.02,880.2 269 60.00 3.593 0.166 3.6 08/26/09 37,210,140.4 271.9 1,840.02,608.7 244 60.00 3.649 0.152 08/26/09 37,092,666.1 269.9 1,840.02,640.9 243 60.00 3.155 0.133

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 4.1 4.1 08/29/09 31,489,861.4 268.7 1,840.02,190.6 199 60.00 3.678 0.129 4.4 08/29/09 32,942,510.4 269.2 1,840.02,255.9 207 60.00 3.736 0.135 4.8 08/29/09 32,968,841.0 270.3 1,840.02,275.6 212 60.00 3.978 0.145 4.3 08/29/09 37,352,009.4 273.3 1,840.02,659.3 248 60.00 4.207 0.179 3.7 08/29/09 31,683,466.6 264.51,840.02,238.5 198 60.00 3.798 0.136 3.6 08/29/09 24,691,009.0 261.3 1,840.0 1,717.6 151 60.00 3.319 0.091 3.1 08/29/09 25,215,669.6 261.9 1,840.0 1,754.2 157 60.00 3.229 0.091 3.3 08/29/09 26,070,762.8 262.0 1,840.0 1,785.3 158 60.00 2.825 0.081 3.4 08/29/09 26,094,353.6 262.51,840.0 1,716.0 157 60.00 3.131 0.086 3.6 08/29/09 25,554,249.0 261.0 1,840.0 1,722.1 153 60.00 3.148 0.087 3.6 08/29/09 24,714,576.1 263.3 1,840.0 1,679.0 152 60.00 3.307 0.089 3.7 08/29/09 27,797,531.2 266.0 1,840.0 1,888.5 171 60.00 3.307 0.100 3.5 08/28/09 31,962,962.9 268.4 1,840.02,206.1 200 60.00 3.345 0.118 4.1 08/28/09 31,481,858.3 268.6 1,840.02,155.8 199 60.00 3.189 0.110 4.6 08/28/09 33,994,986.9 271.8 1,840.02,383.3 224 60.00 3.649 0.139 4.3 08/28/09 37,715,340.2 273.6 1,840.02,685.1 250 60.00 4.032 0.173 4.2 08/28/09 35,859,615.5 271.6 1,840.02,553.1 233 60.00 3.769 0.154 4.6 08/28/09 33,750,121.1 272.51,840.02,366.2 221 60.00 3.738 0.141 5.0 08/28/09 38,182,247.5 275.7 1,840.02,656.1 253 60.00 4.126 0.175 4.8 08/28/09 39,960,909.2 276.1 1,840.02,823.3 269 60.00 4.416 0.199 4.8 08/28/09 40,690,361.7 276.7 1,840.02,919.1 279 60.00 4.175 0.195 4.8 08/28/09 40,846,710.9 277.3 1,840.02,952.5 279 60.00 4.144 0.196 4.9 08/28/09 39,117,982.3 275.9 1,840.02,806.3 264 60.00 4.175 0.187 4.8 08/28/09 39,119,774.1 276.0 1,840.02,806.4 264 60.00 4.262 0.191 5.0 08/28/09 39,325,953.9 275.8 1,840.02,864.0 271 60.00 4.113 0.188 5.1 08/28/09 39,945,091.5 276.2 1,840.02,865.6 273 60.00 4.349 0.199 4.9 08/28/09 39,880,595.1 277.0 1,840.02,817.7 272 60.00 4.504 0.203 4.4 08/28/09 39,561,107.3 275.51,840.02,859.6 270 60.00 4.230 0.193 3.9 08/28/09 38,226,018.4 274.4 1,840.02,763.1 262 60.00 3.798 0.168 3.1 08/28/09 37,221,386.4 271.4 1,840.02,730.9 247 60.00 3.317 0.145 3.3 08/28/09 29,309,694.2 264.51,840.02,086.7 183 60.00 2.717 0.091 3.6 08/28/09 26,579,962.1 263.7 1,840.0 1,834.6 164 60.00 2.983 0.088 3.7 08/28/09 25,723,846.0 263.51,840.0 1,789.5 163 60.00 3.229 0.092 3.4 08/28/09 27,916,170.0 263.51,840.0 1,957.2 174 60.00 3.293 0.103 3.4 08/28/09 26,102,643.0 263.7 1,840.0 1,830.0 166 60.00 3.026 0.089 3.4 08/28/09 27,275,252.7 264.8 1,840.0 1,941.9 175 60.00 2.980 0.093 08/27/09 27,739,056.8 266.4 1,840.0 1,974.9 178 60.00 2.980 0.094

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 3.6 3.8 08/31/09 25,587,015.8 263.6 1,840.0 1,766.1 155 60.00 3.255 0.092 3.8 08/30/09 26,431,939.3 265.2 1,840.0 1,824.4 163 60.00 3.435 0.100 4.3 08/30/09 30,146,349.1 269.1 1,840.02,097.1 195 60.00 3.409 0.114 4.8 08/30/09 32,325,492.1 272.3 1,840.02,283.8 210 60.00 3.798 0.139 5.5 08/30/09 35,922,920.3 274.7 1,840.02,538.0 234 60.00 4.239 0.172 5.7 08/30/09 36,563,797.7 278.4 1,840.02,603.2 244 60.00 4.821 0.201 5.6 08/30/09 37,721,097.1 272.7 1,840.02,624.1 237 60.00 5.113 0.215 5.3 08/30/09 34,169,807.1 269.9 1,840.02,321.3 211 60.00 5.144 0.191 4.9 08/30/09 33,698,844.7 266.7 1,840.02,234.4 204 60.00 4.988 0.178 4.8 08/30/09 28,876,513.8 264.4 1,840.0 1,930.4 167 60.00 4.574 0.141 4.4 08/30/09 28,132,661.4 263.9 1,840.0 1,895.9 162 60.00 4.444 0.135 4.2 08/30/09 28,975,283.2 264.51,840.0 1,905.4 167 60.00 4.175 0.127 4.4 08/30/09 27,087,072.0 262.4 1,840.0 1,869.6 160 60.00 3.797 0.114 4.3 08/30/09 27,541,330.9 263.8 1,840.0 1,841.1 165 60.00 4.107 0.121 4.4 08/30/09 29,257,223.9 262.51,840.0 1,971.7 174 60.00 3.982 0.126 4.2 08/30/09 27,636,675.3 262.8 1,840.0 1,847.5 164 60.00 4.107 0.121 3.8 08/30/09 29,276,401.8 264.2 1,840.0 1,941.1 173 60.00 3.953 0.123 3.9 08/30/09 28,332,787.5 262.9 1,840.0 1,955.6 165 60.00 3.435 0.107 4.4 08/30/09 26,683,906.8 263.0 1,840.0 1,769.3 154 60.00 3.670 0.104 3.7 08/30/09 28,547,052.9 262.6 1,840.0 1,923.8 170 60.00 4.074 0.125 4.0 08/30/09 27,798,464.8 262.3 1,840.0 1,858.2 165 60.00 3.454 0.103 4.2 08/30/09 27,062,384.6 263.4 1,840.0 1,794.3 157 60.00 3.764 0.108 4.3 08/30/09 27,279,572.6 263.9 1,840.0 1,764.3 157 60.00 4.052 0.114 4.7 08/30/09 28,311,595.6 264.51,840.0 1,846.4 163 60.00 4.114 0.121 5.1 08/30/09 27,383,003.7 264.7 1,840.0 1,800.7 160 60.00 4.460 0.128 5.1 08/29/09 29,479,427.5 264.6 1,840.0 1,970.6 175 60.00 4.761 0.150 4.7 08/29/09 29,293,771.1 264.4 1,840.0 1,926.4 174 60.00 4.839 0.149 4.3 08/29/09 30,711,161.9 265.8 1,840.02,019.6 184 60.00 4.460 0.144 4.7 08/29/09 31,152,621.6 270.1 1,840.02,048.6 188 60.00 4.080 0.134 3.6 08/29/09 37,115,578.1 272.3 1,840.02,501.3 229 60.00 4.352 0.174 4.1 08/29/09 30,309,961.5 265.1 1,840.02,059.1 181 60.00 3.307 0.109 4.3 08/29/09 26,779,281.2 265.8 1,840.0 1,775.6 164 60.00 3.859 0.110 4.2 08/29/09 28,385,698.7 268.7 1,840.0 1,990.1 183 60.00 3.827 0.122 4.1 08/29/09 29,873,939.6 267.9 1,840.02,126.9 192 60.00 3.681 0.125 4.1 08/29/09 29,699,975.7 267.2 1,840.02,066.1 191 60.00 3.678 0.122 4.0 08/29/09 30,610,993.5 267.3 1,840.02,129.5 195 60.00 3.678 0.125 08/29/09 32,498,823.9 269.51,840.02,260.8 208 60.00 3.588 0.130

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 3.4 3.6 09/01/09 34,494,464.8 273.0 1,840.02,493.3 224 60.00 2.935 0.117 3.1 09/01/09 33,179,344.9 271.0 1,840.02,362.2 217 60.00 3.155 0.119 3.5 09/01/09 33,045,802.5 271.8 1,840.02,334.8 215 60.00 2.738 0.102 3.5 09/01/09 35,618,534.0 274.0 1,840.02,535.9 233 60.00 3.068 0.124 3.4 09/01/09 35,274,012.7 272.0 1,840.0 1,361.1 226 60.00 5.660 0.123 3.7 09/01/09 33,295,145.3 271.3 1,840.02,352.4 215 60.00 3.003 0.113 3.4 09/01/09 32,838,626.3 267.9 1,840.0 1,731.2 211 60.00 4.380 0.121 3.3 09/01/09 28,323,013.3 265.1 1,840.0 1,431.5 181 60.00 4.198 0.096 2.4 09/01/09 29,582,805.9 266.51,840.02,106.2 192 60.00 2.892 0.097 2.6 09/01/09 27,932,302.3 263.4 1,840.0 1,973.5 173 60.00 2.120 0.067 2.6 09/01/09 25,825,996.6 263.3 1,840.0 1,754.5 155 60.00 2.388 0.067 2.7 09/01/09 25,903,139.0 262.1 1,840.0 1,801.9 157 60.00 2.332 0.067 2.1 09/01/09 24,623,197.8 261.51,840.0 1,699.5 153 60.00 2.441 0.066 2.2 09/01/09 24,855,079.1 262.3 1,840.0 1,715.5 154 60.00 1.899 0.052 2.5 08/31/09 24,598,698.6 263.6 1,840.0 1,684.5 151 60.00 2.005 0.054 2.5 08/31/09 25,451,147.8 266.2 1,840.0 1,742.8 158 60.00 2.278 0.063 3.1 08/31/09 30,341,162.2 270.1 1,840.02,127.2 199 60.00 2.225 0.076 3.5 08/31/09 34,021,299.8 273.4 1,840.02,440.6 226 60.00 2.696 0.105 2.7 08/31/09 38,021,065.7 275.0 1,840.02,768.9 254 60.00 2.999 0.133 3.1 08/31/09 32,194,061.5 269.6 1,840.02,274.6 209 60.00 2.385 0.087 2.8 08/31/09 33,719,253.4 270.3 1,840.02,345.7 219 60.00 2.781 0.104 3.1 08/31/09 33,972,931.5 273.1 1,840.02,437.2 223 60.00 2.435 0.095 3.2 08/31/09 38,322,865.2 276.0 1,840.02,770.1 255 60.00 2.676 0.119 3.3 08/31/09 39,293,408.9 276.4 1,840.02,840.2 262 60.00 2.762 0.125 3.6 08/31/09 39,012,830.6 276.7 1,840.02,841.2 262 60.00 2.828 0.128 4.1 08/31/09 39,241,183.2 277.2 1,840.02,857.8 263 60.00 3.085 0.141 4.2 08/31/09 39,314,060.1 277.6 1,840.02,863.1 264 60.00 3.513 0.161 4.3 08/31/09 39,873,190.1 277.3 1,840.02,882.1 267 60.00 3.626 0.167 3.9 08/31/09 38,990,545.4 276.51,840.02,860.8 261 60.00 3.657 0.167 3.4 08/31/09 39,440,355.1 274.3 1,840.02,915.1 261 60.00 3.293 0.153 3.4 08/31/09 34,673,985.2 269.2 1,840.02,468.6 220 60.00 2.980 0.118 3.6 08/31/09 33,320,984.8 267.6 1,840.02,354.2 208 60.00 3.003 0.113 3.5 08/31/09 29,999,011.4 266.4 1,840.02,103.2 187 60.00 3.204 0.108 3.4 08/31/09 30,816,555.5 263.0 1,840.02,093.5 189 60.00 3.215 0.108 3.4 08/31/09 26,399,825.1 263.2 1,840.0 1,779.1 157 60.00 3.148 0.090 3.6 08/31/09 26,046,762.0 263.4 1,840.0 1,727.0 157 60.00 3.200 0.088 08/31/09 26,933,283.5 264.51,840.0 1,844.3 160 60.00 3.280 0.097

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 MC M 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 2.0 2.1 09/03/09 28,072,850.6 265.4 1,840.0 1,861.4 169 60.00 1.882 0.056 2.8 09/03/09 26,887,694.5 264.7 1,840.0 1,797.4 161 60.00 1.960 0.056 2.6 09/03/09 24,825,339.6 263.3 1,840.0 1,659.5 149 60.00 2.614 0.069 2.6 09/02/09 24,622,123.1 264.8 1,840.0 1,645.9 149 60.00 2.427 0.064 2.3 09/02/09 28,762,036.0 267.2 1,840.0 1,938.3 179 60.00 2.407 0.075 3.5 09/02/09 29,480,001.7 270.0 1,840.0 1,986.7 187 60.00 2.130 0.068 3.9 09/02/09 33,933,267.6 277.1 1,840.02,323.7 222 60.00 3.189 0.119 3.2 09/02/09 41,046,426.6 281.3 1,840.02,966.9 276 60.00 3.367 0.160 3.7 09/02/09 34,430,402.3 275.0 1,840.02,507.4 231 60.00 2.742 0.110 3.6 09/02/09 37,499,493.0 279.6 1,840.02,710.5 256 60.00 3.194 0.138 3.7 09/02/09 40,077,268.9 281.4 1,840.02,940.4 275 60.00 3.062 0.144 3.8 09/02/09 40,949,409.4 281.8 1,840.03,004.4 281 60.00 3.147 0.151 3.8 09/02/09 41,105,015.4 281.8 1,840.02,993.5 281 60.00 3.256 0.156 4.1 09/02/09 41,139,117.0 282.2 1,840.02,996.0 282 60.00 3.256 0.156 4.0 09/02/09 41,061,239.8 281.7 1,840.03,012.6 282 60.00 3.487 0.168 3.7 09/02/09 40,859,004.4 280.9 1,840.02,997.8 282 60.00 3.402 0.163 3.8 09/02/09 40,889,600.1 281.7 1,840.03,022.3 283 60.00 3.124 0.151 3.9 09/02/09 41,124,815.2 281.7 1,840.03,039.7 283 60.00 3.208 0.156 3.7 09/02/09 41,243,232.3 281.9 1,840.03,048.4 282 60.00 3.293 0.160 3.7 09/02/09 41,091,212.2 281.9 1,840.03,037.2 282 60.00 3.124 0.152 3.2 09/02/09 39,590,462.4 274.7 1,840.02,904.7 265 60.00 3.147 0.146 2.7 09/02/09 31,361,456.9 266.51,840.02,164.6 199 60.00 2.893 0.100 2.7 09/02/09 26,996,369.8 264.6 1,840.0 1,819.3 164 60.00 2.500 0.073 2.7 09/02/09 27,168,338.9 265.4 1,840.0 1,816.1 165 60.00 2.520 0.073 3.1 09/02/09 26,143,495.7 264.2 1,840.0 1,705.0 156 60.00 2.583 0.070 3.1 09/02/09 24,802,463.6 263.4 1,840.0 1,698.4 151 60.00 2.825 0.077 3.5 09/02/09 24,583,688.0 263.4 1,840.0 1,656.7 151 60.00 2.870 0.076 3.1 09/01/09 26,029,415.5 263.7 1,840.0 1,824.9 162 60.00 3.115 0.091 2.9 09/01/09 25,295,677.3 264.0 1,840.0 1,759.7 156 60.00 2.781 0.078 2.9 09/01/09 27,191,632.7 264.8 1,840.0 1,891.6 167 60.00 2.601 0.079 2.9 09/01/09 25,740,127.4 265.4 1,840.0 1,720.7 156 60.00 2.707 0.074 2.7 09/01/09 30,167,524.5 268.0 1,840.02,033.1 189 60.00 2.685 0.087 3.0 09/01/09 26,193,374.0 264.4 1,840.0 1,864.8 165 60.00 2.366 0.071 2.8 09/01/09 26,798,183.3 266.9 1,840.0 1,878.8 171 60.00 2.670 0.080 2.8 09/01/09 31,066,442.3 269.7 1,840.02,194.9 203 60.00 2.473 0.087 3.4 09/01/09 31,366,046.1 270.2 1,840.02,233.1 202 60.00 2.454 0.088 09/01/09 32,597,603.7 272.7 1,840.02,338.6 211 60.00 2.957 0.111

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 C 08:00 C 09:00 C 10:00 C 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 4.5 4.3 09/04/09 40,992,414.8 285.4 1,840.02,918.5 271 60.00 3.944 0.184 4.2 09/04/09 40,103,841.3 283.0 1,840.02,898.8 265 60.00 3.712 0.172 4.6 09/04/09 38,736,980.5 282.2 1,840.02,757.9 256 60.00 3.681 0.162 5.4 09/04/09 39,181,343.0 282.51,840.02,810.8 260 60.00 4.001 0.180 6.2 09/04/09 41,014,275.6 283.9 1,840.02,964.6 274 60.00 4.662 0.221 5.8 09/04/09 40,508,826.8 282.1 1,840.02,928.1 269 60.00 5.352 0.251 5.6 09/04/09 37,493,329.6 278.9 1,840.02,628.6 240 60.00 5.162 0.217 5.4 09/04/09 36,098,101.2 275.8 1,840.02,550.4 228 60.00 4.946 0.202 5.3 09/04/09 30,461,797.0 274.6 1,840.02,102.5 195 60.00 4.882 0.164 4.9 09/04/09 32,234,602.9 274.0 1,840.02,260.0 207 60.00 4.717 0.170 4.5 09/04/09 30,619,943.9 268.9 1,840.02,096.8 188 60.00 4.465 0.150 4.3 09/04/09 26,861,869.1 267.7 1,840.0 1,810.3 165 60.00 4.167 0.121 4.3 09/04/09 25,709,146.0 266.0 1,840.0 1,690.6 154 60.00 4.080 0.110 4.4 09/04/09 26,367,475.4 266.7 1,840.0 1,690.9 153 60.00 4.184 0.113 4.4 09/04/09 25,995,612.3 266.6 1,840.0 1,709.5 158 60.00 4.175 0.114 4.5 09/04/09 26,347,220.9 267.9 1,840.0 1,746.9 163 60.00 4.141 0.116 4.4 09/03/09 27,074,460.9 266.51,840.0 1,824.6 166 60.00 4.167 0.122 4.4 09/03/09 26,862,372.6 269.9 1,840.0 1,810.3 171 60.00 4.074 0.118 5.1 09/03/09 31,578,615.0 274.0 1,840.02,145.3 202 60.00 4.042 0.139 5.6 09/03/09 34,861,253.5 279.8 1,840.02,406.2 229 60.00 4.611 0.177 4.7 09/03/09 39,389,556.5 278.6 1,840.02,804.4 258 60.00 4.908 0.220 4.8 09/03/09 30,682,633.7 270.7 1,840.02,067.8 193 60.00 4.352 0.144 5.4 09/03/09 33,221,890.5 275.51,840.02,275.0 217 60.00 4.374 0.159 5.3 09/03/09 40,067,528.6 281.9 1,840.02,765.6 267 60.00 4.882 0.216 4.7 09/03/09 42,200,983.3 282.6 1,840.02,958.7 282 60.00 4.717 0.223 4.7 09/03/09 41,807,051.3 281.8 1,840.02,931.0 278 60.00 4.183 0.196 4.5 09/03/09 41,602,897.1 281.6 1,840.02,939.3 279 60.00 4.151 0.195 4.2 09/03/09 41,599,003.7 281.3 1,840.02,961.7 280 60.00 3.944 0.187 3.9 09/03/09 41,541,510.6 281.2 1,840.02,957.6 278 60.00 3.681 0.174 3.0 09/03/09 41,717,984.4 281.0 1,840.02,970.1 278 60.00 3.418 0.162 3.0 09/03/09 39,385,365.7 277.8 1,840.02,761.2 260 60.00 2.670 0.118 2.6 09/03/09 38,639,418.4 278.1 1,840.02,687.9 254 60.00 2.691 0.116 2.4 09/03/09 37,452,261.8 275.2 1,840.02,585.0 242 60.00 2.351 0.097 2.4 09/03/09 35,934,875.4 273.51,840.02,460.8 230 60.00 2.187 0.086 1.3 09/03/09 33,058,987.7 266.4 1,840.02,281.8 207 60.00 2.170 0.079 2.2 09/03/09 25,328,695.6 264.4 1,840.0 1,720.7 155 60.00 1.194 0.033 09/03/09 27,071,526.9 266.0 1,840.0 1,750.9 164 60.00 2.123 0.059

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 2.4 0.0 09/06/09 1,086,441.1 102.4 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 1,084,324.4 103.3 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 7,587,489.7 104.4 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 1,117,686.8 105.51,840.0 0.0 0 0.00 0.000 0.0 09/06/09 1,127,178.4 106.6 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,153,650.3 107.8 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,168,559.1 109.0 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,107,739.4 110.2 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,147,074.2 111.6 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,199,827.2 112.9 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,225,879.4 114.4 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,253,109.1 115.9 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,260,357.1 117.51,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,375,744.8 119.1 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,451,498.0 120.7 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,453,420.5 122.2 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,476,262.5 123.6 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,550,960.0 125.1 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,582,940.1 126.9 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,613,605.3 128.9 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,604,054.7 131.3 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,591,401.2 134.51,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,593,534.7 138.0 1,840.0 0.0 0 0.00 0.000 2.5 09/05/09 1,440,985.3 142.9 1,840.0 0.0 0 0.00 0.000 0.0 09/05/09 1,386,871.4 149.4 1,840.0 0.0 0 0.00 0.000 0.1 09/05/09 1,234,078.2 159.2 1,840.0 0.0 0 0.00 0.000 0.1 09/05/09 7,723,472.7 177.51,840.0 0.0 0 0.00 0.000 1.8 09/05/09 9,930,055.6 222.0 1,840.0 0.0 0 0.00 0.000 3.0 09/05/09 25,202,770.3 255.9 1,840.0 739.7 53 53.00 3.827 0.040 4.1 09/04/09 26,421,361.5 264.51,840.0 1,464.6 126 60.00 3.377 0.079 5.0 09/04/09 25,797,622.1 269.6 1,840.0 1,682.5 163 60.00 3.923 0.106 5.2 09/04/09 33,433,803.2 277.0 1,840.02,325.8 219 60.00 4.485 0.167 4.4 09/04/09 34,537,060.7 274.7 1,840.02,421.3 221 60.00 4.628 0.179 4.2 09/04/09 32,173,328.9 271.3 1,840.02,203.2 204 60.00 4.009 0.141 4.1 09/04/09 27,023,893.1 268.2 1,840.0 1,806.5 164 60.00 3.921 0.113 4.1 09/04/09 27,561,405.1 271.8 1,840.0 1,857.4 173 60.00 3.796 0.113 09/04/09 33,366,366.2 278.2 1,840.02,321.1 218 60.00 3.678 0.136

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 F F F F F F F F F 17:00 F F F F F F F F F 18:00 F F F F F F F F F 19:00 F F F F F F F F F 20:00 F F F F F F F F F 21:00 F F F F F F F F F 22:00 F F F F F F F F F 23:00 F F F F F F F F F 00:00 F F F F F F F F F 01:00 F F F F F F F F F 02:00 FC F F F F F F F F 03:00 F F F F F F F F F 04:00 F F F F F F F F FC 05:00 FC F F F F F F F FC 06:00 F F F F F F F F F 07:00 F F F F F F F F F 08:00 F F F F F F F F F 09:00 F F F F F F F F F 10:00 F F F F F F F F F 11:00 F F F F F F F F F 12:00 F F F F F F F F F 13:00 F F F F F F F F F 14:00 F F F F F F F F F 15:00 F F F F F F F F F 16:00 17:00 0.1 0.0 09/07/09 28,035,396.7 152.9 1,840.0 137.1 0 60.00 1.276 0.003 0.0 09/07/09 27,588,502.5 136.51,840.0 90.0 0 44.00 0.000 0.000 0.0 09/07/09 2,388,798.9 92.0 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 648,184.3 90.1 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 646,257.8 90.0 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 667,837.3 89.9 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 724,302.0 89.9 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 728,309.8 89.8 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 763,964.7 89.7 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 697,919.3 89.4 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 664,197.2 89.0 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 663,948.5 89.1 1,840.0 0.0 0 0.00 0.000 2.4 09/07/09 720,284.2 89.6 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 749,226.5 90.1 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 776,811.6 90.7 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 7,345,548.4 91.51,840.0 0.0 0 0.00 0.000 0.0 09/07/09 786,752.6 92.2 1,840.0 0.0 0 0.00 0.000 0.0 09/07/09 812,798.3 92.9 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 787,661.8 93.6 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 811,528.1 94.3 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 804,822.9 95.0 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 790,695.7 95.7 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 831,174.7 96.4 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 819,021.0 97.0 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 912,556.9 97.7 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 915,571.5 98.0 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 965,328.3 98.3 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 980,103.8 98.51,840.0 0.0 0 0.00 0.000 0.0 09/06/09 980,899.5 98.6 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 996,233.1 98.6 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 990,333.5 98.6 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 942,962.2 98.8 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 1,047,473.2 99.0 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 1,039,105.4 99.4 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 1,078,948.8 99.8 1,840.0 0.0 0 0.00 0.000 0.0 09/06/09 1,114,630.3 100.6 1,840.0 0.0 0 0.00 0.000 09/06/09 1,053,940.7 101.4 1,840.0 0.0 0 0.00 0.000

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 C 19:00 S S SC 20:00 21:00 C 22:00 C 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 5.2 4.9 09/09/09 37,984,349.2 278.8 1,840.02,601.1 244 60.00 4.738 0.197 4.1 09/09/09 33,515,761.4 273.1 1,840.02,295.1 207 60.00 4.465 0.164 4.1 09/09/09 27,737,666.0 269.0 1,840.0 1,854.2 164 60.00 3.827 0.113 4.2 09/09/09 26,706,508.2 268.6 1,840.0 1,785.3 158 60.00 3.827 0.109 4.4 09/09/09 26,431,813.7 267.3 1,840.0 1,752.6 158 60.00 3.953 0.111 4.1 09/09/09 26,151,134.4 267.4 1,840.0 1,748.1 156 60.00 4.107 0.115 4.3 09/09/09 26,346,646.0 269.0 1,840.0 1,732.6 154 60.00 3.890 0.108 4.0 09/08/09 26,662,279.6 270.6 1,840.0 1,782.3 160 60.00 4.014 0.114 4.0 09/08/09 26,304,427.8 270.9 1,840.0 1,758.4 157 60.00 3.734 0.105 4.7 09/08/09 27,512,694.1 277.8 1,840.0 1,794.3 169 60.00 3.827 0.110 5.4 09/08/09 35,468,116.2 290.51,840.02,448.1 232 60.00 4.249 0.166 5.5 09/08/09 42,278,973.2 295.6 1,840.03,033.1 283 60.00 4.697 0.228 5.6 09/08/09 41,663,554.8 291.9 1,840.02,988.9 278 60.00 4.784 0.229 5.6 09/08/09 40,927,292.5 290.1 1,840.02,936.1 273 60.00 4.871 0.229 5.5 09/08/09 41,442,902.5 290.9 1,840.02,973.1 277 60.00 4.871 0.232 5.4 09/08/09 42,422,897.6 289.7 1,840.03,043.4 284 60.00 4.784 0.233 5.2 09/08/09 41,635,215.2 287.3 1,840.03,009.5 278 60.00 4.662 0.224 5.5 09/08/09 42,271,226.8 288.0 1,840.03,055.5 281 60.00 4.489 0.219 4.9 09/08/09 44,142,033.6 288.7 1,840.03,070.7 284 60.00 4.933 0.242 5.0 09/08/09 41,997,635.3 288.0 1,840.02,921.6 270 60.00 4.395 0.205 5.3 09/08/09 40,742,549.5 286.7 1,840.02,812.2 257 60.00 4.520 0.203 4.8 09/08/09 40,440,245.4 287.9 1,840.02,747.3 254 60.00 4.868 0.214 4.3 09/08/09 39,257,356.1 284.8 1,840.02,624.2 241 60.00 4.481 0.188 4.0 09/08/09 34,373,643.5 277.6 1,840.02,372.6 207 60.00 3.887 0.147 4.0 09/08/09 29,942,348.8 266.9 1,840.0 1,985.3 181 60.00 3.764 0.120 3.1 09/08/09 28,591,743.6 258.9 1,840.0 1,942.4 177 60.00 3.674 0.114 2.4 09/08/09 28,905,476.1 247.8 1,840.0 1,743.7 154 60.00 3.207 0.089 1.6 09/08/09 24,042,397.9 235.1 1,840.0 1,071.4 88 60.00 3.360 0.058 1.6 09/08/09 22,736,071.2 225.51,840.0 790.8 62 60.00 2.870 0.036 1.6 09/08/09 23,482,050.4 220.6 1,840.0 561.5 36 60.00 4.175 0.037 0.7 09/08/09 28,266,958.2 220.0 1,840.0 537.7 25 60.00 5.249 0.045 0.6 09/07/09 26,446,558.2 215.8 1,840.0 373.7 12 60.00 3.091 0.018 0.6 09/07/09 25,756,889.1 214.3 1,840.0 322.0 7 60.00 2.995 0.015 0.3 09/07/09 24,683,170.2 206.7 1,840.0 308.5 0 60.00 2.995 0.015 0.2 09/07/09 26,959,184.1 194.1 1,840.0 219.8 0 60.00 2.296 0.008 0.1 09/07/09 27,257,662.7 188.2 1,840.0 118.5 0 52.00 2.870 0.005 09/07/09 27,444,119.3 173.6 1,840.0 149.2 0 60.00 1.148 0.003

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 4.8 5.1 09/10/09 41,917,548.4 294.1 1,840.02,984.4 280 60.00 4.207 0.201 5.1 09/10/09 42,447,584.3 291.2 1,840.03,022.1 285 60.00 4.470 0.216 5.1 09/10/09 42,316,955.0 289.4 1,840.03,012.8 284 60.00 4.470 0.215 5.0 09/10/09 43,019,785.3 288.9 1,840.03,062.8 287 60.00 4.470 0.219 4.8 09/10/09 43,256,639.7 288.0 1,840.03,079.7 287 60.00 4.382 0.216 4.5 09/10/09 42,656,439.8 287.51,840.03,060.1 284 60.00 4.175 0.204 4.5 09/10/09 42,424,442.8 287.8 1,840.03,043.5 284 60.00 3.914 0.190 4.5 09/10/09 42,152,613.8 289.1 1,840.03,046.9 282 60.00 3.885 0.189 4.7 09/10/09 42,127,198.8 288.7 1,840.03,022.2 280 60.00 3.914 0.189 4.9 09/10/09 42,533,279.9 290.7 1,840.03,051.3 282 60.00 4.088 0.199 4.9 09/10/09 42,141,919.5 292.0 1,840.03,023.2 278 60.00 4.262 0.206 4.5 09/10/09 41,429,158.3 289.1 1,840.02,949.6 272 60.00 4.295 0.203 4.8 09/10/09 38,754,726.3 282.7 1,840.02,717.1 250 60.00 4.005 0.174 4.5 09/10/09 35,241,768.1 277.9 1,840.02,432.5 225 60.00 4.340 0.169 3.8 09/10/09 32,022,825.4 271.6 1,840.02,210.3 201 60.00 4.068 0.144 3.7 09/10/09 29,006,086.4 270.2 1,840.0 1,939.0 179 60.00 3.547 0.110 4.2 09/10/09 26,804,073.3 269.7 1,840.0 1,689.8 160 60.00 3.662 0.099 4.2 09/10/09 28,725,946.5 273.6 1,840.0 1,826.6 180 60.00 4.122 0.120 4.2 09/10/09 32,205,543.0 275.51,840.02,205.4 203 60.00 3.827 0.135 4.3 09/10/09 33,774,062.0 277.1 1,840.02,331.1 215 60.00 3.797 0.142 4.0 09/09/09 32,952,264.1 274.4 1,840.02,220.7 203 60.00 3.982 0.141 4.2 09/09/09 31,137,013.9 276.4 1,840.02,098.4 195 60.00 3.704 0.124 4.9 09/09/09 33,854,135.7 281.2 1,840.02,355.1 219 60.00 3.767 0.142 4.8 09/09/09 40,146,368.9 285.8 1,840.02,923.7 269 60.00 4.198 0.196 4.7 09/09/09 41,726,861.3 287.1 1,840.03,038.8 280 60.00 4.113 0.200 4.6 09/09/09 40,533,941.8 284.4 1,840.02,885.8 268 60.00 4.119 0.190 4.7 09/09/09 40,251,527.3 286.7 1,840.02,865.8 267 60.00 4.032 0.185 5.0 09/09/09 42,658,841.5 290.9 1,840.03,083.5 286 60.00 4.057 0.200 4.7 09/09/09 42,584,397.9 289.4 1,840.03,101.2 286 60.00 4.284 0.212 4.9 09/09/09 41,470,213.5 287.8 1,840.03,020.1 278 60.00 4.027 0.194 5.1 09/09/09 42,538,938.9 288.2 1,840.03,074.8 283 60.00 4.230 0.208 5.0 09/09/09 41,437,790.1 286.1 1,840.02,950.2 272 60.00 4.470 0.211 5.4 09/09/09 41,417,156.1 286.8 1,840.02,926.2 271 60.00 4.416 0.207 4.8 09/09/09 40,948,311.1 286.2 1,840.02,937.6 269 60.00 4.697 0.221 5.0 09/09/09 32,764,246.9 274.2 1,840.02,314.8 205 60.00 4.239 0.157 5.5 09/09/09 34,400,555.0 282.7 1,840.02,374.4 226 60.00 4.520 0.172 09/09/09 40,921,355.4 282.3 1,840.02,935.6 269 60.00 4.784 0.225

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 4.9 4.1 09/12/09 39,475,140.0 272.9 1,840.02,724.6 250 60.00 4.430 0.193 4.2 09/12/09 28,449,367.7 264.51,840.0 1,948.1 170 60.00 3.736 0.116 4.1 09/12/09 24,875,139.8 263.4 1,840.0 1,716.9 150 60.00 3.797 0.104 4.2 09/12/09 24,555,651.7 264.1 1,840.0 1,708.2 149 60.00 3.678 0.100 4.4 09/12/09 24,759,058.0 265.9 1,840.0 1,695.5 149 60.00 3.827 0.104 4.6 09/12/09 25,660,579.3 266.1 1,840.0 1,757.2 154 60.00 4.009 0.113 4.8 09/12/09 25,599,518.7 266.1 1,840.0 1,697.4 151 60.00 4.329 0.118 4.8 09/12/09 25,538,973.4 266.0 1,840.0 1,707.2 154 60.00 4.481 0.122 5.0 09/12/09 26,038,746.7 266.0 1,840.0 1,797.3 158 60.00 4.340 0.125 4.7 09/11/09 26,468,878.0 267.4 1,840.0 1,769.4 162 60.00 4.667 0.132 4.6 09/11/09 28,756,792.3 270.9 1,840.0 1,938.0 184 60.00 4.352 0.135 5.0 09/11/09 32,710,644.8 273.9 1,840.02,311.1 215 60.00 4.063 0.150 5.7 09/11/09 37,762,125.9 279.51,840.02,668.0 250 60.00 4.416 0.188 5.6 09/11/09 40,403,437.6 282.0 1,840.02,876.5 269 60.00 4.996 0.230 5.4 09/11/09 39,653,388.1 279.0 1,840.02,823.1 262 60.00 4.908 0.222 6.0 09/11/09 37,044,604.0 278.6 1,840.02,597.2 243 60.00 4.806 0.200 6.0 09/11/09 41,544,415.6 281.3 1,840.02,957.8 278 60.00 5.259 0.249 6.0 09/11/09 41,661,935.2 281.8 1,840.02,966.2 279 60.00 5.259 0.249 6.1 09/11/09 41,071,445.9 281.8 1,840.02,901.8 273 60.00 5.299 0.246 6.1 09/11/09 43,048,476.2 283.6 1,840.03,041.4 286 60.00 5.388 0.262 6.1 09/11/09 42,907,393.9 284.1 1,840.03,054.8 287 60.00 5.346 0.261 6.1 09/11/09 42,424,300.0 283.51,840.03,020.4 286 60.00 5.346 0.258 5.2 09/11/09 42,837,177.1 284.51,840.03,049.8 286 60.00 5.346 0.261 4.8 09/11/09 42,540,335.8 284.51,840.03,051.8 284 60.00 4.523 0.221 5.3 09/11/09 42,485,185.9 282.4 1,840.03,001.7 283 60.00 4.239 0.203 5.4 09/11/09 38,824,029.6 277.4 1,840.02,743.0 256 60.00 4.681 0.205 5.3 09/11/09 39,051,862.0 277.3 1,840.02,759.1 255 60.00 4.769 0.210 3.6 09/11/09 36,609,869.6 275.2 1,840.02,507.0 233 60.00 4.830 0.194 4.2 09/11/09 31,580,749.5 268.6 1,840.02,179.8 193 60.00 3.255 0.113 4.5 09/11/09 26,103,494.9 265.3 1,840.0 1,759.1 157 60.00 3.889 0.109 4.2 09/11/09 25,792,076.1 265.1 1,840.0 1,682.1 155 60.00 4.306 0.116 4.3 09/11/09 26,045,949.5 266.6 1,840.0 1,698.7 155 60.00 4.019 0.109 4.8 09/11/09 26,303,868.6 267.3 1,840.0 1,672.6 155 60.00 4.220 0.113 4.9 09/10/09 27,176,928.5 269.3 1,840.0 1,728.1 161 60.00 4.710 0.130 4.8 09/10/09 28,992,753.5 273.7 1,840.0 1,906.6 177 60.00 4.650 0.142 4.6 09/10/09 32,499,857.9 278.8 1,840.02,243.2 208 60.00 4.340 0.156 09/10/09 37,466,257.5 285.9 1,840.02,626.7 245 60.00 4.094 0.172

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 3.1 3.3 09/13/09 29,558,322.1 268.1 1,840.02,040.1 190 60.00 2.803 0.091 3.7 09/13/09 30,059,074.0 272.0 1,840.02,058.4 194 60.00 3.007 0.099 3.7 09/13/09 37,955,612.8 278.51,840.02,702.3 253 60.00 3.243 0.140 3.8 09/13/09 41,496,064.3 281.2 1,840.02,999.4 280 60.00 3.194 0.153 3.5 09/13/09 41,107,951.4 279.7 1,840.02,971.4 279 60.00 3.280 0.156 3.5 09/13/09 41,304,714.5 279.7 1,840.02,963.2 281 60.00 3.044 0.144 3.8 09/13/09 41,454,919.6 281.7 1,840.02,996.5 280 60.00 3.021 0.145 4.2 09/13/09 41,525,600.0 281.1 1,840.03,024.2 281 60.00 3.256 0.157 4.5 09/13/09 41,354,945.0 281.1 1,840.02,989.2 278 60.00 3.626 0.173 4.6 09/13/09 42,027,723.8 280.0 1,840.03,037.9 286 60.00 3.885 0.189 3.9 09/13/09 41,152,549.0 276.9 1,840.02,952.3 277 60.00 4.001 0.189 3.7 09/13/09 38,215,318.9 272.51,840.02,720.7 253 60.00 3.418 0.149 4.0 09/13/09 34,640,791.1 271.7 1,840.02,409.8 223 60.00 3.319 0.128 3.1 09/13/09 35,020,201.0 270.6 1,840.02,474.2 219 60.00 3.533 0.140 4.1 09/13/09 28,148,066.4 264.6 1,840.0 1,866.3 163 60.00 2.917 0.087 4.3 09/13/09 25,198,567.5 263.4 1,840.0 1,684.5 149 60.00 3.827 0.103 4.0 09/13/09 25,118,027.1 263.4 1,840.0 1,692.7 150 60.00 3.982 0.108 3.8 09/13/09 24,397,604.7 263.3 1,840.0 1,684.0 150 60.00 3.616 0.097 3.9 09/13/09 24,853,881.0 263.1 1,840.0 1,674.9 152 60.00 3.519 0.094 4.0 09/13/09 24,937,078.0 262.7 1,840.0 1,680.5 151 60.00 3.611 0.097 4.3 09/13/09 24,679,909.4 263.1 1,840.0 1,649.8 150 60.00 3.734 0.099 4.1 09/13/09 26,642,523.0 264.1 1,840.0 1,781.0 161 60.00 4.014 0.114 3.4 09/12/09 25,989,245.1 263.7 1,840.0 1,737.3 154 60.00 3.827 0.106 3.2 09/12/09 25,904,742.0 264.3 1,840.0 1,731.7 154 60.00 3.174 0.088 4.0 09/12/09 25,505,630.3 267.9 1,840.0 1,718.9 154 60.00 2.963 0.081 4.5 09/12/09 33,701,752.5 274.6 1,840.02,344.5 219 60.00 3.588 0.135 4.9 09/12/09 39,911,227.4 278.8 1,840.02,798.1 264 60.00 4.005 0.179 4.5 09/12/09 38,617,483.4 277.1 1,840.02,728.4 256 60.00 4.328 0.189 4.4 09/12/09 39,657,030.2 278.6 1,840.02,823.4 267 60.00 3.944 0.178 4.8 09/12/09 41,324,333.0 280.7 1,840.02,964.5 280 60.00 3.827 0.181 5.0 09/12/09 42,296,895.1 282.3 1,840.03,034.4 286 60.00 4.175 0.203 4.9 09/12/09 41,892,869.9 280.7 1,840.03,005.4 282 60.00 4.349 0.209 5.3 09/12/09 39,262,655.9 280.0 1,840.02,774.0 260 60.00 4.328 0.192 5.2 09/12/09 42,416,165.8 281.3 1,840.03,042.9 287 60.00 4.610 0.224 4.9 09/12/09 41,687,482.8 279.7 1,840.02,990.6 282 60.00 4.523 0.216 5.1 09/12/09 41,868,162.8 280.0 1,840.02,980.8 283 60.00 4.295 0.205 09/12/09 42,067,624.2 280.7 1,840.02,995.1 284 60.00 4.470 0.214

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 M 09:00 S S S 10:00 C 4.8 4.6 09/15/09 42,107,548.3 282.4 1,840.03,043.7 287 60.00 4.144 0.202 4.4 09/15/09 42,163,276.7 283.51,840.03,024.7 287 60.00 4.001 0.194 4.4 09/15/09 41,270,757.7 281.3 1,840.02,960.7 278 60.00 3.827 0.181 4.3 09/15/09 38,372,055.4 275.9 1,840.02,752.8 253 60.00 3.827 0.168 4.6 09/15/09 37,472,928.8 277.3 1,840.02,647.5 246 60.00 3.798 0.161 3.5 09/15/09 39,630,731.1 279.0 1,840.02,843.1 263 60.00 4.001 0.182 3.2 09/15/09 32,871,117.6 268.1 1,840.02,322.4 207 60.00 3.091 0.115 3.4 09/15/09 27,929,219.1 266.51,840.0 1,912.5 177 60.00 2.916 0.089 3.0 09/15/09 25,835,744.2 265.9 1,840.0 1,783.2 163 60.00 3.074 0.088 3.3 09/15/09 27,199,643.9 267.9 1,840.0 1,907.0 170 60.00 2.670 0.081 3.3 09/15/09 27,865,606.4 269.7 1,840.0 1,938.5 176 60.00 2.960 0.092 3.5 09/14/09 30,167,774.2 269.8 1,840.02,131.4 189 60.00 2.915 0.099 4.8 09/14/09 27,325,821.8 271.6 1,840.0 1,930.6 174 60.00 3.091 0.095 4.7 09/14/09 34,780,803.4 278.7 1,840.02,495.2 234 60.00 4.175 0.167 4.5 09/14/09 40,641,994.8 283.51,840.02,959.8 279 60.00 4.027 0.191 4.3 09/14/09 41,404,250.1 281.9 1,840.03,015.3 285 60.00 3.856 0.186 4.3 09/14/09 41,753,608.8 280.7 1,840.02,995.4 285 60.00 3.740 0.179 4.7 09/14/09 42,129,247.9 281.6 1,840.02,976.5 283 60.00 3.798 0.181 4.4 09/14/09 41,819,807.5 281.51,840.02,954.7 281 60.00 4.151 0.196 4.6 09/14/09 42,628,946.5 281.3 1,840.02,988.7 284 60.00 3.916 0.187 4.9 09/14/09 42,293,311.5 282.9 1,840.02,965.1 282 60.00 4.094 0.194 4.6 09/14/09 42,591,867.8 283.3 1,840.02,986.1 285 60.00 4.361 0.208 4.7 09/14/09 43,118,291.2 283.2 1,840.03,022.9 287 60.00 4.094 0.198 4.8 09/14/09 42,783,075.5 282.3 1,840.02,999.5 285 60.00 4.183 0.201 4.6 09/14/09 43,330,035.7 283.51,840.03,037.8 286 60.00 4.272 0.208 4.3 09/14/09 42,757,121.7 282.6 1,840.03,020.9 287 60.00 4.063 0.196 3.6 09/14/09 40,920,711.8 276.8 1,840.02,868.9 268 60.00 3.827 0.176 4.0 09/14/09 35,392,223.9 270.3 1,840.02,442.8 224 60.00 3.255 0.127 4.3 09/14/09 33,354,332.4 268.8 1,840.02,265.9 214 60.00 3.674 0.133 4.0 09/14/09 32,820,148.3 269.1 1,840.02,229.6 213 60.00 3.950 0.141 3.3 09/14/09 32,889,361.4 268.2 1,840.02,270.1 207 60.00 3.616 0.131 3.2 09/14/09 28,388,791.2 264.9 1,840.0 1,928.6 171 60.00 3.031 0.093 3.5 09/14/09 24,926,473.6 264.3 1,840.0 1,639.2 150 60.00 3.036 0.080 3.5 09/14/09 25,312,493.2 263.4 1,840.0 1,705.8 152 60.00 3.241 0.088 3.8 09/14/09 24,737,862.0 263.8 1,840.0 1,653.7 150 60.00 3.267 0.086 3.2 09/13/09 25,959,324.9 265.0 1,840.0 1,763.5 159 60.00 3.490 0.098 09/13/09 26,637,283.2 266.2 1,840.0 1,838.5 167 60.00 2.893 0.085

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 S S SC 12:00 S S SC 13:00 S S SC 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 4.2 3.8 09/16/09 26,996,629.4 266.0 1,840.0 1,775.3 162 60.00 3.985 0.113 4.6 09/16/09 25,418,113.6 268.0 1,840.0 1,713.0 158 60.00 3.519 0.096 5.1 09/16/09 31,753,099.1 272.8 1,840.02,226.2 207 60.00 4.094 0.146 5.1 09/16/09 34,742,217.0 273.6 1,840.02,398.0 226 60.00 4.611 0.177 5.8 09/16/09 37,289,754.0 278.8 1,840.02,614.4 247 60.00 4.539 0.190 5.7 09/16/09 41,156,300.7 281.3 1,840.02,930.1 277 60.00 5.083 0.238 5.8 09/16/09 40,774,228.3 279.9 1,840.02,880.8 273 60.00 5.034 0.232 6.1 09/16/09 41,405,458.9 281.8 1,840.02,925.4 280 60.00 5.123 0.240 5.8 09/16/09 42,089,870.6 281.9 1,840.02,996.6 286 60.00 5.346 0.256 6.0 09/16/09 42,189,388.0 281.2 1,840.03,003.7 285 60.00 5.083 0.244 6.1 09/16/09 42,343,506.8 282.0 1,840.02,968.7 283 60.00 5.340 0.254 5.4 09/16/09 41,977,047.6 282.8 1,840.02,965.8 280 60.00 5.388 0.255 5.6 09/16/09 42,431,529.0 282.3 1,840.03,021.0 287 60.00 4.733 0.229 5.0 09/16/09 42,196,602.1 281.51,840.03,004.2 286 60.00 4.908 0.236 5.5 09/16/09 39,584,394.0 277.51,840.02,775.2 259 60.00 4.450 0.197 5.9 09/16/09 41,244,860.5 282.0 1,840.02,891.6 274 60.00 4.895 0.226 5.6 09/16/09 41,921,479.3 281.3 1,840.02,961.8 279 60.00 5.211 0.247 5.8 09/16/09 39,485,298.7 279.1 1,840.02,746.8 259 60.00 5.023 0.221 4.5 09/16/09 38,234,672.3 274.8 1,840.02,659.8 245 60.00 5.203 0.221 5.2 09/16/09 30,336,129.8 269.7 1,840.02,027.9 192 60.00 4.201 0.136 4.3 09/16/09 32,034,709.8 268.4 1,840.02,158.9 202 60.00 4.815 0.166 4.1 09/16/09 27,855,787.6 265.1 1,840.0 1,877.3 175 60.00 3.982 0.120 4.1 09/16/09 25,472,556.2 264.2 1,840.0 1,744.3 153 60.00 3.736 0.104 3.8 09/16/09 25,716,969.7 265.0 1,840.0 1,733.1 155 60.00 3.796 0.105 3.9 09/15/09 26,732,900.5 268.0 1,840.0 1,801.6 164 60.00 3.519 0.101 4.6 09/15/09 26,993,538.9 270.8 1,840.0 1,848.5 170 60.00 3.554 0.105 5.5 09/15/09 34,702,436.3 280.8 1,840.02,451.8 230 60.00 4.063 0.159 5.5 09/15/09 40,901,447.9 286.1 1,840.02,978.7 277 60.00 4.713 0.224 5.5 09/15/09 41,666,413.1 285.1 1,840.03,034.4 284 60.00 4.713 0.229 5.3 09/15/09 41,646,281.4 284.2 1,840.03,032.9 285 60.00 4.713 0.229 5.5 09/15/09 42,044,913.6 284.7 1,840.03,062.0 285 60.00 4.541 0.222 5.5 09/15/09 42,138,541.9 283.51,840.03,000.1 285 60.00 4.821 0.231 5.5 09/15/09 42,481,284.5 284.1 1,840.03,001.4 286 60.00 4.858 0.233 5.2 09/15/09 42,395,794.0 284.9 1,840.03,018.4 287 60.00 4.821 0.233 5.2 09/15/09 42,382,322.7 283.1 1,840.03,040.4 287 60.00 4.523 0.220 5.2 09/15/09 42,370,336.6 282.6 1,840.03,039.6 287 60.00 4.523 0.220 09/15/09 42,444,328.4 282.51,840.03,044.9 287 60.00 4.523 0.220

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 4.8 5.3 09/18/09 41,150,544.9 292.8 1,840.02,974.5 278 60.00 4.144 0.197 5.1 09/18/09 41,042,661.8 290.8 1,840.02,922.1 275 60.00 4.645 0.217 4.7 09/18/09 41,279,386.2 291.0 1,840.02,938.9 275 60.00 4.470 0.210 3.8 09/18/09 41,159,971.1 286.8 1,840.02,952.8 272 60.00 4.088 0.193 3.0 09/18/09 36,607,461.2 276.4 1,840.02,566.5 233 60.00 3.382 0.139 3.1 09/18/09 34,257,551.4 273.1 1,840.02,420.4 213 60.00 2.650 0.103 2.4 09/18/09 33,848,992.8 269.0 1,840.02,317.9 211 60.00 2.825 0.105 3.1 09/18/09 28,497,004.7 264.2 1,840.0 1,951.4 174 60.00 2.187 0.068 3.4 09/18/09 27,267,317.2 261.51,840.0 1,867.2 164 60.00 2.825 0.084 3.9 09/18/09 25,610,838.3 262.6 1,840.0 1,753.8 157 60.00 3.098 0.087 3.7 09/18/09 25,917,084.0 264.4 1,840.0 1,774.8 157 60.00 3.554 0.101 3.7 09/18/09 25,452,819.9 264.2 1,840.0 1,729.1 154 60.00 3.399 0.094 3.5 09/18/09 25,393,330.5 264.51,840.0 1,711.3 154 60.00 3.426 0.094 3.4 09/17/09 26,295,763.2 266.7 1,840.0 1,786.4 161 60.00 3.215 0.092 3.7 09/17/09 27,135,205.0 269.8 1,840.0 1,858.2 169 60.00 3.098 0.092 4.0 09/17/09 31,286,553.0 272.51,840.02,193.5 198 60.00 3.293 0.116 4.8 09/17/09 33,406,710.2 276.51,840.02,305.8 215 60.00 3.616 0.133 5.3 09/17/09 40,060,890.3 281.8 1,840.02,808.6 266 60.00 4.272 0.192 5.2 09/17/09 42,025,060.7 283.2 1,840.02,969.2 280 60.00 4.681 0.222 5.0 09/17/09 42,253,628.9 282.3 1,840.02,916.4 276 60.00 4.701 0.219 5.0 09/17/09 42,627,566.5 282.6 1,840.02,988.6 282 60.00 4.450 0.213 5.3 09/17/09 42,655,756.7 283.51,840.02,967.4 278 60.00 4.485 0.213 5.5 09/17/09 42,676,749.9 283.8 1,840.02,968.8 278 60.00 4.754 0.226 6.1 09/17/09 42,995,507.3 283.51,840.02,967.7 277 60.00 4.972 0.236 6.1 09/17/09 43,333,606.1 283.51,840.02,991.0 280 60.00 5.515 0.264 5.6 09/17/09 43,455,194.3 281.6 1,840.02,975.7 282 60.00 5.559 0.264 5.3 09/17/09 42,502,443.8 279.2 1,840.02,887.4 275 60.00 5.144 0.237 4.9 09/17/09 42,208,815.1 279.4 1,840.02,867.5 273 60.00 4.868 0.223 4.7 09/17/09 39,340,366.2 277.51,840.02,715.3 249 60.00 4.430 0.192 4.8 09/17/09 38,796,528.5 275.7 1,840.02,635.7 241 60.00 4.317 0.182 4.5 09/17/09 37,523,265.0 275.51,840.02,528.7 233 60.00 4.444 0.180 3.6 09/17/09 33,272,958.1 267.7 1,840.02,260.4 200 60.00 4.133 0.149 4.0 09/17/09 27,408,880.4 264.9 1,840.0 1,772.6 162 60.00 3.473 0.098 3.5 09/17/09 28,048,840.4 265.0 1,840.0 1,798.8 166 60.00 3.892 0.112 4.2 09/17/09 26,717,856.1 264.8 1,840.0 1,713.4 158 60.00 3.406 0.093 4.3 09/17/09 25,964,744.7 265.8 1,840.0 1,636.9 150 60.00 4.157 0.109 09/17/09 28,022,788.6 267.9 1,840.0 1,842.8 170 60.00 4.080 0.120

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 2.8 2.8 09/20/09 25,390,230.5 262.9 1,840.0 1,669.7 150 60.00 2.657 0.071 2.6 09/20/09 26,725,791.7 263.3 1,840.0 1,786.6 159 60.00 2.614 0.075 2.4 09/19/09 25,225,531.8 262.6 1,840.0 1,727.4 151 60.00 2.369 0.065 2.7 09/19/09 24,938,014.7 263.51,840.0 1,707.7 152 60.00 2.187 0.060 3.0 09/19/09 26,207,151.8 264.51,840.0 1,780.4 159 60.00 2.480 0.071 3.5 09/19/09 28,576,504.1 269.2 1,840.0 1,910.3 179 60.00 2.800 0.086 3.0 09/19/09 34,411,813.9 272.9 1,840.02,431.3 225 60.00 3.091 0.120 2.6 09/19/09 34,744,541.3 262.6 1,840.02,454.8 220 60.00 2.650 0.104 2.7 09/19/09 30,164,864.6 264.8 1,840.02,082.0 192 60.00 2.351 0.078 2.8 09/19/09 35,372,537.3 269.8 1,840.02,480.0 230 60.00 2.403 0.095 2.6 09/19/09 36,088,935.2 272.51,840.02,549.8 234 60.00 2.473 0.101 2.5 09/19/09 37,694,946.8 272.1 1,840.02,683.7 246 60.00 2.279 0.098 2.3 09/19/09 34,518,989.0 267.2 1,840.02,438.8 224 60.00 2.208 0.086 1.9 09/19/09 31,905,002.0 263.3 1,840.02,219.5 206 60.00 2.063 0.073 2.4 09/19/09 30,141,076.7 264.3 1,840.02,080.4 192 60.00 1.718 0.057 2.4 09/19/09 31,843,772.8 265.4 1,840.02,215.2 203 60.00 2.153 0.076 2.8 09/19/09 33,500,433.5 269.4 1,840.02,312.2 215 60.00 2.170 0.080 2.5 09/19/09 35,608,083.4 267.51,840.02,477.1 227 60.00 2.512 0.099 2.2 09/19/09 30,598,227.8 264.9 1,840.02,111.9 194 60.00 2.260 0.076 2.2 09/19/09 29,784,764.1 263.2 1,840.02,039.6 179 60.00 2.005 0.065 2.3 09/19/09 26,901,807.4 261.51,840.0 1,827.6 162 60.00 2.021 0.059 2.4 09/19/09 25,309,403.7 259.0 1,840.0 1,705.6 150 60.00 2.130 0.058 2.5 09/19/09 26,913,534.5 258.8 1,840.0 1,828.4 162 60.00 2.204 0.064 2.2 09/19/09 25,547,990.1 258.1 1,840.0 1,763.4 157 60.00 2.260 0.064 2.2 09/19/09 25,902,266.3 259.4 1,840.0 1,787.8 159 60.00 1.989 0.057 2.4 09/19/09 25,854,959.2 261.8 1,840.0 1,756.5 158 60.00 2.021 0.057 2.6 09/18/09 26,186,885.7 265.9 1,840.0 1,779.0 158 60.00 2.204 0.063 3.0 09/18/09 27,973,815.4 272.8 1,840.0 1,900.4 174 60.00 2.388 0.073 3.4 09/18/09 32,897,450.0 283.0 1,840.02,306.4 216 60.00 2.670 0.098 4.4 09/18/09 38,334,074.2 288.8 1,840.02,750.0 256 60.00 2.957 0.130 4.7 09/18/09 40,134,046.4 292.8 1,840.02,901.0 270 60.00 3.798 0.176 4.5 09/18/09 41,137,975.5 292.3 1,840.02,995.9 279 60.00 4.027 0.193 4.2 09/18/09 40,209,058.4 289.3 1,840.02,928.3 271 60.00 3.856 0.181 4.1 09/18/09 40,279,605.5 290.6 1,840.02,911.5 272 60.00 3.626 0.169 4.5 09/18/09 40,776,560.3 291.8 1,840.02,947.5 274 60.00 3.539 0.167 4.8 09/18/09 40,491,880.3 292.0 1,840.02,904.9 271 60.00 3.914 0.182 09/18/09 40,855,816.4 292.9 1,840.02,931.0 272 60.00 4.175 0.196

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 4.1 4.0 09/21/09 42,040,360.8 281.9 1,840.03,015.9 286 60.00 3.566 0.172 3.9 09/21/09 41,995,639.8 281.9 1,840.03,012.8 284 60.00 3.479 0.168 4.5 09/21/09 42,382,556.4 282.8 1,840.03,040.5 286 60.00 3.392 0.165 4.0 09/21/09 42,239,283.6 281.4 1,840.03,053.1 287 60.00 3.885 0.190 4.3 09/21/09 42,032,349.0 281.0 1,840.03,038.2 286 60.00 3.453 0.168 4.4 09/21/09 41,390,405.4 280.51,840.02,969.3 280 60.00 3.740 0.178 4.3 09/21/09 41,619,294.6 280.7 1,840.02,985.7 280 60.00 3.827 0.183 4.4 09/21/09 41,873,317.8 279.51,840.02,958.4 279 60.00 3.798 0.180 3.8 09/21/09 40,048,819.5 275.2 1,840.02,807.8 259 60.00 3.916 0.176 3.1 09/21/09 32,957,320.9 266.1 1,840.02,274.7 202 60.00 3.435 0.125 3.0 09/21/09 27,756,714.5 265.3 1,840.0 1,825.3 166 60.00 2.942 0.086 2.6 09/21/09 27,732,960.1 264.2 1,840.0 1,793.6 163 60.00 2.895 0.083 2.9 09/21/09 27,158,518.6 262.3 1,840.0 1,741.7 158 60.00 2.530 0.070 2.6 09/21/09 25,560,526.8 261.7 1,840.0 1,667.0 152 60.00 2.775 0.074 3.4 09/21/09 24,938,173.5 263.7 1,840.0 1,653.5 148 60.00 2.447 0.065 3.7 09/20/09 26,366,549.4 265.7 1,840.0 1,762.6 160 60.00 3.174 0.089 3.6 09/20/09 28,131,684.0 265.9 1,840.0 1,880.6 170 60.00 3.454 0.104 3.6 09/20/09 27,464,636.2 265.2 1,840.0 1,836.0 169 60.00 3.360 0.099 4.5 09/20/09 28,643,669.2 270.7 1,840.0 1,945.9 183 60.00 3.307 0.103 3.8 09/20/09 36,465,479.3 276.51,840.02,556.5 240 60.00 4.005 0.164 3.9 09/20/09 35,382,006.3 271.1 1,840.02,442.1 224 60.00 3.435 0.134 3.9 09/20/09 33,061,322.8 271.8 1,840.02,264.0 215 60.00 3.554 0.129 3.7 09/20/09 33,549,089.6 268.2 1,840.02,315.6 214 60.00 3.526 0.131 3.8 09/20/09 30,941,518.8 270.4 1,840.02,118.9 200 60.00 3.372 0.114 3.6 09/20/09 32,256,232.9 268.3 1,840.02,208.8 201 60.00 3.463 0.122 3.4 09/20/09 32,170,068.9 268.6 1,840.02,185.5 203 60.00 3.307 0.116 3.1 09/20/09 29,241,268.3 266.2 1,840.0 1,986.5 185 60.00 3.123 0.099 3.3 09/20/09 29,972,960.5 267.9 1,840.02,036.2 191 60.00 2.847 0.093 3.5 09/20/09 30,183,620.9 269.1 1,840.02,066.9 190 60.00 3.007 0.099 3.4 09/20/09 32,793,050.6 270.7 1,840.02,299.1 209 60.00 3.115 0.115 3.4 09/20/09 31,244,995.2 268.9 1,840.02,156.6 195 60.00 3.074 0.106 2.8 09/20/09 30,520,435.9 266.6 1,840.02,090.0 192 60.00 3.098 0.104 2.7 09/20/09 29,252,869.4 264.1 1,840.0 1,971.4 180 60.00 2.593 0.082 3.0 09/20/09 26,676,642.4 263.8 1,840.0 1,768.8 160 60.00 2.541 0.072 2.8 09/20/09 27,095,372.5 263.0 1,840.0 1,752.3 158 60.00 2.895 0.081 3.0 09/20/09 25,965,068.6 262.6 1,840.0 1,693.4 152 60.00 2.679 0.073 09/20/09 26,537,221.4 262.9 1,840.0 1,745.1 158 60.00 2.847 0.079

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 3.2 3.8 09/23/09 27,867,745.2 264.51,840.0 1,847.8 167 60.00 3.012 0.089 3.7 09/23/09 27,280,627.5 263.3 1,840.0 1,719.9 160 60.00 3.761 0.103 3.8 09/23/09 26,935,099.9 263.6 1,840.0 1,727.4 155 60.00 3.600 0.099 4.1 09/23/09 26,291,623.3 264.6 1,840.0 1,757.6 159 60.00 3.547 0.100 3.8 09/22/09 27,427,591.3 267.4 1,840.0 1,863.3 171 60.00 3.766 0.112 3.9 09/22/09 33,472,851.1 271.9 1,840.02,255.8 210 60.00 3.519 0.127 4.5 09/22/09 37,149,924.9 275.4 1,840.02,584.3 238 60.00 3.498 0.145 4.7 09/22/09 38,302,287.9 277.2 1,840.02,726.9 253 60.00 3.944 0.172 4.4 09/22/09 40,184,682.1 278.51,840.02,882.8 270 60.00 4.088 0.188 4.5 09/22/09 40,528,216.9 279.51,840.02,929.5 275 60.00 3.798 0.178 4.4 09/22/09 40,445,930.2 278.9 1,840.02,945.5 273 60.00 3.856 0.182 4.3 09/22/09 40,566,638.7 280.0 1,840.02,932.3 273 60.00 3.798 0.178 4.8 09/22/09 42,163,182.3 281.8 1,840.03,047.7 286 60.00 3.712 0.181 5.0 09/22/09 41,893,081.1 281.4 1,840.03,028.1 286 60.00 4.144 0.201 5.2 09/22/09 42,266,397.8 284.0 1,840.03,032.1 285 60.00 4.349 0.211 4.9 09/22/09 42,429,872.9 283.0 1,840.03,067.0 287 60.00 4.489 0.220 4.9 09/22/09 42,075,783.7 281.7 1,840.03,018.5 286 60.00 4.262 0.206 4.2 09/22/09 42,161,538.8 280.9 1,840.03,047.6 287 60.00 4.230 0.206 4.2 09/22/09 41,710,869.6 280.8 1,840.02,992.3 282 60.00 3.653 0.175 4.0 09/22/09 41,492,791.9 280.0 1,840.02,931.6 277 60.00 3.709 0.174 4.1 09/22/09 39,525,698.8 276.9 1,840.02,771.1 258 60.00 3.560 0.158 4.1 09/22/09 38,643,413.1 277.9 1,840.02,709.2 255 60.00 3.649 0.158 3.4 09/22/09 38,730,428.7 275.0 1,840.02,736.4 256 60.00 3.621 0.158 3.2 09/22/09 34,140,618.7 269.1 1,840.02,356.5 213 60.00 3.074 0.116 3.0 09/22/09 28,915,074.3 265.51,840.0 1,964.3 173 60.00 2.939 0.092 3.0 09/22/09 25,499,541.9 264.3 1,840.0 1,746.2 151 60.00 2.734 0.076 3.0 09/22/09 25,388,264.2 266.3 1,840.0 1,738.5 151 60.00 2.734 0.076 2.8 09/22/09 28,919,245.6 267.4 1,840.0 1,980.3 175 60.00 2.734 0.087 2.9 09/21/09 28,971,207.6 268.0 1,840.0 1,889.4 172 60.00 2.679 0.081 3.6 09/21/09 30,113,545.6 270.9 1,840.02,013.1 186 60.00 2.707 0.087 3.9 09/21/09 35,951,688.1 277.51,840.02,501.0 238 60.00 3.229 0.129 3.9 09/21/09 38,742,487.1 280.0 1,840.02,737.2 260 60.00 3.444 0.151 4.3 09/21/09 41,789,715.2 284.51,840.02,975.3 282 60.00 3.418 0.163 4.3 09/21/09 42,158,406.1 283.7 1,840.03,024.4 285 60.00 3.740 0.181 4.2 09/21/09 40,587,632.8 280.7 1,840.02,911.7 275 60.00 3.740 0.174 4.1 09/21/09 40,722,991.3 280.2 1,840.02,921.4 276 60.00 3.653 0.171 09/21/09 41,321,188.6 280.8 1,840.02,986.8 281 60.00 3.539 0.169

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 4.4 4.2 09/24/09 41,605,315.0 281.4 1,840.02,984.7 278 60.00 3.827 0.183 4.4 09/24/09 41,682,927.2 280.9 1,840.02,967.6 276 60.00 3.681 0.175 4.6 09/24/09 42,140,133.4 282.1 1,840.03,023.1 281 60.00 3.827 0.185 4.6 09/24/09 41,707,131.0 281.1 1,840.02,969.4 275 60.00 4.032 0.191 4.6 09/24/09 41,382,286.7 281.6 1,840.02,968.7 276 60.00 4.001 0.190 4.7 09/24/09 42,173,869.2 281.8 1,840.03,025.5 282 60.00 4.001 0.194 5.3 09/24/09 42,462,374.1 281.9 1,840.03,000.0 282 60.00 4.151 0.199 5.6 09/24/09 42,364,182.4 282.0 1,840.03,016.1 281 60.00 4.645 0.224 5.4 09/24/09 42,468,385.7 281.6 1,840.03,023.5 281 60.00 4.908 0.237 5.3 09/24/09 40,992,551.0 279.0 1,840.02,918.5 269 60.00 4.733 0.221 5.2 09/24/09 41,439,494.8 279.6 1,840.02,972.8 276 60.00 4.610 0.219 3.7 09/24/09 40,624,072.9 277.4 1,840.02,870.2 264 60.00 4.593 0.211 3.8 09/24/09 33,515,230.2 270.51,840.02,331.5 209 60.00 3.319 0.124 3.9 09/24/09 30,017,193.7 267.51,840.02,071.8 183 60.00 3.435 0.114 4.0 09/24/09 27,581,740.8 267.0 1,840.0 1,828.8 167 60.00 3.670 0.107 4.0 09/24/09 28,621,817.7 268.6 1,840.0 1,928.9 174 60.00 3.704 0.114 4.1 09/24/09 29,419,616.0 268.2 1,840.0 1,998.6 177 60.00 3.674 0.117 4.5 09/23/09 28,494,238.4 269.7 1,840.0 1,904.8 172 60.00 3.827 0.117 4.7 09/23/09 30,456,485.9 271.9 1,840.02,085.6 191 60.00 4.101 0.137 5.1 09/23/09 32,530,872.1 272.51,840.02,280.7 209 60.00 4.183 0.153 5.5 09/23/09 34,674,232.1 276.8 1,840.02,430.9 226 60.00 4.539 0.176 5.4 09/23/09 40,288,278.5 280.4 1,840.02,824.5 262 60.00 4.895 0.221 5.2 09/23/09 40,304,028.9 279.8 1,840.02,847.6 264 60.00 4.769 0.217 5.9 09/23/09 38,559,362.0 280.2 1,840.02,724.3 252 60.00 4.593 0.200 6.2 09/23/09 41,967,493.9 283.4 1,840.03,033.5 283 60.00 5.093 0.247 5.8 09/23/09 41,720,502.9 283.51,840.03,015.7 281 60.00 5.352 0.258 5.4 09/23/09 42,555,714.6 284.4 1,840.03,076.1 286 60.00 5.007 0.246 5.3 09/23/09 42,987,679.2 283.8 1,840.03,060.6 287 60.00 4.733 0.232 5.1 09/23/09 42,996,565.7 283.7 1,840.03,061.2 287 60.00 4.645 0.227 4.7 09/23/09 42,271,738.9 282.2 1,840.03,055.5 286 60.00 4.403 0.215 4.8 09/23/09 41,632,215.0 281.2 1,840.03,031.9 282 60.00 4.027 0.195 4.8 09/23/09 41,417,122.0 281.3 1,840.03,016.2 278 60.00 4.113 0.198 4.6 09/23/09 42,377,839.9 282.1 1,840.03,063.2 283 60.00 4.144 0.203 4.6 09/23/09 42,934,036.0 281.1 1,840.03,080.0 286 60.00 4.001 0.197 4.5 09/23/09 40,892,289.8 279.51,840.02,911.3 267 60.00 4.032 0.188 3.2 09/23/09 38,271,265.7 273.0 1,840.02,724.7 244 60.00 3.944 0.172 09/23/09 29,921,177.7 264.9 1,840.02,081.5 184 60.00 2.870 0.096

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 4.3 4.4 09/26/09 33,836,959.7 271.6 1,840.02,280.3 211 60.00 3.982 0.145 4.0 09/26/09 32,882,841.6 271.0 1,840.02,180.3 203 60.00 4.141 0.144 3.9 09/26/09 32,473,770.8 268.4 1,840.02,117.9 195 60.00 3.827 0.130 3.6 09/26/09 27,222,830.4 264.9 1,840.0 1,790.2 162 60.00 3.701 0.106 3.6 09/26/09 26,219,893.1 265.6 1,840.0 1,767.0 159 60.00 3.333 0.094 3.4 09/26/09 27,686,414.2 267.3 1,840.0 1,880.8 169 60.00 3.307 0.099 2.9 09/25/09 26,595,253.1 267.4 1,840.0 1,821.2 162 60.00 3.098 0.090 3.7 09/25/09 26,029,395.6 269.6 1,840.0 1,768.3 160 60.00 2.664 0.075 4.6 09/25/09 35,068,709.0 280.4 1,840.02,420.5 228 60.00 3.345 0.129 4.6 09/25/09 40,930,343.9 284.4 1,840.02,936.3 274 60.00 4.001 0.188 4.6 09/25/09 41,235,259.6 284.1 1,840.02,980.6 277 60.00 3.971 0.189 4.6 09/25/09 41,389,410.1 284.6 1,840.02,991.7 279 60.00 3.971 0.190 4.4 09/25/09 41,864,993.2 283.2 1,840.03,026.1 282 60.00 3.971 0.192 4.4 09/25/09 40,727,870.1 281.2 1,840.02,921.8 272 60.00 3.827 0.179 4.5 09/25/09 41,225,076.8 281.0 1,840.02,935.0 275 60.00 3.856 0.181 4.5 09/25/09 41,861,476.7 282.0 1,840.02,980.3 277 60.00 3.944 0.188 4.7 09/25/09 42,317,503.7 282.2 1,840.02,989.9 281 60.00 3.974 0.190 4.8 09/25/09 42,407,183.3 282.6 1,840.02,996.1 282 60.00 4.151 0.199 4.8 09/25/09 41,978,421.8 282.51,840.02,988.7 282 60.00 4.207 0.201 4.5 09/25/09 41,363,104.8 281.0 1,840.02,967.3 278 60.00 4.175 0.198 4.6 09/25/09 41,842,792.4 280.51,840.02,979.0 281 60.00 3.944 0.188 5.0 09/25/09 42,019,245.4 280.7 1,840.02,991.6 281 60.00 4.032 0.193 4.9 09/25/09 42,273,491.9 280.8 1,840.03,009.7 282 60.00 4.382 0.211 5.0 09/25/09 42,142,817.4 279.51,840.02,977.5 279 60.00 4.328 0.206 3.8 09/25/09 39,678,548.1 275.2 1,840.02,825.0 259 60.00 4.382 0.198 3.5 09/25/09 32,114,804.2 268.6 1,840.02,199.2 198 60.00 3.463 0.122 2.8 09/25/09 30,188,932.8 268.3 1,840.02,018.1 186 60.00 3.267 0.105 3.4 09/25/09 28,646,968.6 266.4 1,840.0 1,821.6 170 60.00 2.748 0.080 3.3 09/25/09 27,853,416.2 266.7 1,840.0 1,861.9 171 60.00 3.174 0.094 3.2 09/25/09 27,784,384.0 268.2 1,840.0 1,887.5 174 60.00 3.031 0.091 3.4 09/24/09 29,866,245.2 270.51,840.02,045.2 189 60.00 2.916 0.095 3.8 09/24/09 30,063,577.3 272.8 1,840.02,058.7 191 60.00 3.098 0.102 3.9 09/24/09 36,099,887.4 277.2 1,840.02,511.3 234 60.00 3.409 0.137 4.5 09/24/09 38,540,079.9 282.0 1,840.02,722.9 254 60.00 3.444 0.150 4.2 09/24/09 41,829,972.9 284.3 1,840.02,978.1 281 60.00 3.944 0.188 4.1 09/24/09 42,124,859.4 283.1 1,840.02,999.1 282 60.00 3.681 0.177 09/24/09 42,117,117.6 281.8 1,840.02,952.8 279 60.00 3.649 0.172

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 5.7 5.6 09/27/09 40,065,827.5 281.51,840.02,787.2 267 60.00 5.113 0.228 4.9 09/27/09 41,254,178.5 279.6 1,840.02,869.8 273 60.00 5.023 0.231 5.1 09/27/09 34,582,730.8 274.6 1,840.02,349.4 223 60.00 4.501 0.169 4.5 09/27/09 35,582,506.3 274.9 1,840.02,456.0 227 60.00 4.611 0.181 4.3 09/27/09 28,193,357.7 267.51,840.0 1,915.3 170 60.00 4.133 0.127 4.7 09/27/09 26,697,459.9 267.7 1,840.0 1,784.6 163 60.00 4.014 0.115 4.6 09/27/09 27,047,574.2 266.6 1,840.0 1,837.5 169 60.00 4.317 0.127 4.1 09/27/09 24,353,970.4 265.4 1,840.0 1,654.5 152 60.00 4.225 0.112 4.3 09/27/09 26,442,622.7 266.0 1,840.0 1,825.1 164 60.00 3.707 0.108 4.4 09/27/09 28,575,115.4 272.2 1,840.0 1,894.6 183 60.00 4.047 0.123 5.1 09/27/09 29,118,085.8 269.4 1,840.0 1,978.1 181 60.00 4.042 0.128 4.4 09/27/09 29,849,646.7 268.3 1,840.02,027.9 185 60.00 4.684 0.152 4.9 09/27/09 25,852,487.4 265.51,840.0 1,700.0 158 60.00 4.175 0.113 4.1 09/27/09 27,412,926.0 264.8 1,840.0 1,743.1 165 60.00 4.809 0.134 4.4 09/27/09 26,139,110.7 265.2 1,840.0 1,647.9 154 60.00 4.058 0.107 4.8 09/27/09 26,098,504.1 265.0 1,840.0 1,659.6 152 60.00 4.318 0.115 4.9 09/27/09 26,584,045.1 266.1 1,840.0 1,675.9 155 60.00 4.751 0.127 4.8 09/27/09 27,250,241.0 266.51,840.0 1,777.2 163 60.00 4.688 0.133 4.4 09/27/09 26,385,136.2 265.0 1,840.0 1,778.1 160 60.00 4.444 0.126 3.6 09/26/09 25,561,632.0 264.51,840.0 1,694.9 155 60.00 4.141 0.112 3.9 09/26/09 26,103,494.0 266.1 1,840.0 1,716.6 157 60.00 3.416 0.094 4.7 09/26/09 27,830,463.7 270.4 1,840.0 1,754.5 170 60.00 3.860 0.108 5.2 09/26/09 35,744,116.4 279.51,840.02,428.3 232 60.00 4.317 0.168 5.4 09/26/09 42,266,543.6 283.0 1,840.02,940.3 278 60.00 4.664 0.219 5.0 09/26/09 42,555,419.8 281.3 1,840.02,937.2 277 60.00 4.882 0.229 5.0 09/26/09 42,590,500.8 280.1 1,840.02,893.4 271 60.00 4.593 0.212 4.9 09/26/09 41,879,113.6 281.51,840.02,890.6 273 60.00 4.520 0.209 5.0 09/26/09 41,888,900.6 280.8 1,840.02,891.3 273 60.00 4.430 0.205 5.1 09/26/09 42,019,730.4 281.6 1,840.02,923.1 275 60.00 4.485 0.210 4.9 09/26/09 42,305,203.1 281.51,840.02,943.0 275 60.00 4.575 0.215 5.1 09/26/09 41,649,875.5 280.2 1,840.02,874.8 271 60.00 4.430 0.204 5.2 09/26/09 42,320,294.7 280.7 1,840.02,921.0 276 60.00 4.611 0.215 5.0 09/26/09 42,074,332.5 280.8 1,840.02,904.0 275 60.00 4.701 0.218 4.8 09/26/09 42,403,753.0 280.7 1,840.02,926.8 276 60.00 4.520 0.212 5.1 09/26/09 41,660,149.2 281.1 1,840.02,898.1 273 60.00 4.306 0.200 4.7 09/26/09 40,053,711.4 277.3 1,840.02,764.6 259 60.00 4.611 0.204 09/26/09 37,102,637.3 273.4 1,840.02,480.3 234 60.00 4.387 0.174

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 4.5 4.5 09/29/09 39,998,975.0 278.51,840.02,869.5 268 60.00 3.914 0.180 4.7 09/29/09 38,878,074.4 279.0 1,840.02,767.9 258 60.00 3.944 0.175 3.4 09/29/09 40,453,358.0 277.8 1,840.02,902.1 268 60.00 4.088 0.190 3.5 09/29/09 32,461,877.3 266.7 1,840.02,258.2 203 60.00 3.050 0.110 3.5 09/29/09 27,331,781.9 265.6 1,840.0 1,827.1 165 60.00 3.267 0.095 3.6 09/29/09 25,588,433.9 264.9 1,840.0 1,752.2 155 60.00 3.189 0.089 4.0 09/29/09 25,471,671.3 264.2 1,840.0 1,716.6 150 60.00 3.333 0.091 3.4 09/29/09 25,320,439.6 263.51,840.0 1,692.6 152 60.00 3.734 0.101 3.4 09/28/09 25,859,301.6 265.0 1,840.0 1,742.7 159 60.00 3.148 0.088 2.9 09/28/09 26,477,012.5 265.1 1,840.0 1,784.3 160 60.00 3.148 0.090 3.1 09/28/09 25,886,141.4 266.4 1,840.0 1,702.3 157 60.00 2.752 0.075 3.9 09/28/09 29,216,502.5 270.9 1,840.0 1,969.0 185 60.00 2.870 0.090 4.7 09/28/09 34,891,995.7 277.8 1,840.02,408.3 231 60.00 3.526 0.136 4.0 09/28/09 40,547,671.5 281.1 1,840.02,864.8 272 60.00 4.151 0.190 3.7 09/28/09 37,548,932.1 275.7 1,840.02,652.9 247 60.00 3.533 0.150 3.6 09/28/09 35,349,724.6 274.0 1,840.02,420.7 228 60.00 3.372 0.131 3.6 09/28/09 35,320,081.5 274.4 1,840.02,437.8 231 60.00 3.255 0.127 4.3 09/28/09 35,828,568.4 276.1 1,840.02,473.0 234 60.00 3.255 0.129 4.7 09/28/09 36,061,779.0 278.4 1,840.02,528.3 236 60.00 3.827 0.155 4.3 09/28/09 40,543,982.2 281.8 1,840.02,842.5 269 60.00 4.183 0.190 3.8 09/28/09 39,131,243.0 277.2 1,840.02,722.2 253 60.00 3.857 0.168 4.6 09/28/09 34,754,494.9 275.1 1,840.02,398.8 228 60.00 3.435 0.132 4.8 09/28/09 37,659,845.8 278.6 1,840.02,599.4 248 60.00 4.159 0.173 4.7 09/28/09 40,362,084.5 280.2 1,840.02,807.8 267 60.00 4.306 0.193 4.6 09/28/09 38,333,704.8 278.0 1,840.02,687.5 253 60.00 4.183 0.180 4.3 09/28/09 37,468,426.3 275.8 1,840.02,606.5 243 60.00 4.126 0.172 4.5 09/28/09 32,658,050.0 269.1 1,840.02,218.6 205 60.00 3.950 0.140 4.7 09/28/09 29,063,280.7 270.3 1,840.0 1,895.4 181 60.00 4.306 0.130 4.7 09/28/09 30,719,337.0 270.7 1,840.02,020.1 190 60.00 4.460 0.144 4.2 09/28/09 29,309,745.1 266.1 1,840.0 1,943.4 178 60.00 4.423 0.137 4.2 09/28/09 25,183,642.7 263.51,840.0 1,615.1 151 60.00 4.087 0.106 3.8 09/28/09 25,427,506.0 265.8 1,840.0 1,630.7 156 60.00 4.087 0.107 3.2 09/27/09 27,011,834.2 266.51,840.0 1,776.3 163 60.00 3.606 0.102 3.6 09/27/09 26,147,365.2 267.1 1,840.0 1,719.4 156 60.00 3.036 0.083 4.3 09/27/09 27,706,057.3 273.2 1,840.0 1,806.9 174 60.00 3.444 0.100 5.2 09/27/09 34,023,573.6 276.9 1,840.02,366.9 222 60.00 3.857 0.146 09/27/09 37,074,629.2 280.6 1,840.02,559.0 245 60.00 4.701 0.192

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 S S SC 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 * * 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 4.5 4.0 09/30/09 37,426,155.4 276.6 1,840.02,664.6 249 60.00 3.944 0.168 4.0 09/30/09 39,943,935.6 279.2 1,840.02,909.0 272 60.00 3.427 0.159 3.8 09/30/09 40,503,573.2 279.0 1,840.02,949.7 276 60.00 3.427 0.162 4.0 09/30/09 38,082,689.2 276.3 1,840.02,732.0 253 60.00 3.305 0.144 4.8 09/30/09 37,556,087.2 277.4 1,840.02,673.8 248 60.00 3.506 0.150 4.4 09/30/09 40,835,489.4 279.8 1,840.02,973.9 278 60.00 4.113 0.196 4.2 09/30/09 40,108,461.4 278.51,840.02,899.1 272 60.00 3.798 0.176 4.2 09/30/09 40,333,816.6 278.6 1,840.02,915.4 270 60.00 3.626 0.169 4.4 09/30/09 40,189,113.2 278.8 1,840.02,883.1 269 60.00 3.653 0.168 4.7 09/30/09 39,991,285.9 279.1 1,840.02,847.2 266 60.00 3.856 0.176 4.5 09/30/09 41,220,498.9 279.6 1,840.02,957.1 278 60.00 4.088 0.193 4.6 09/30/09 40,848,325.0 277.4 1,840.02,908.2 275 60.00 3.944 0.183 4.5 09/30/09 41,639,950.0 279.2 1,840.02,942.0 278 60.00 4.063 0.191 3.9 09/30/09 41,655,627.1 278.3 1,840.02,875.2 280 60.00 4.068 0.187 4.3 09/30/09 39,057,071.2 275.7 1,840.02,780.7 258 60.00 3.418 0.152 3.0 09/30/09 39,067,567.7 274.9 1,840.02,802.7 260 60.00 3.740 0.168 2.5 09/30/09 34,533,434.0 267.3 1,840.02,439.8 223 60.00 2.650 0.103 2.5 09/30/09 29,779,470.4 266.0 1,840.02,071.6 191 60.00 2.242 0.074 2.5 09/30/09 27,824,335.9 264.51,840.0 1,875.1 173 60.00 2.315 0.069 2.5 09/30/09 27,815,456.7 264.8 1,840.0 1,904.7 171 60.00 2.278 0.069 2.6 09/30/09 26,969,322.9 264.9 1,840.0 1,832.1 168 60.00 2.296 0.067 2.7 09/29/09 28,317,745.6 266.6 1,840.0 1,939.2 177 60.00 2.369 0.073 3.3 09/29/09 27,544,264.1 267.2 1,840.0 1,871.2 172 60.00 2.480 0.074 4.5 09/29/09 31,217,425.8 272.51,840.02,103.8 201 60.00 3.056 0.103 4.1 09/29/09 37,698,584.9 278.2 1,840.02,643.0 250 60.00 4.005 0.169 4.0 09/29/09 40,947,601.2 280.1 1,840.02,915.3 275 60.00 3.593 0.168 3.9 09/29/09 41,309,289.1 279.51,840.02,941.0 278 60.00 3.506 0.165 4.1 09/29/09 41,434,303.5 279.8 1,840.02,949.9 279 60.00 3.418 0.161 4.6 09/29/09 40,662,292.9 279.51,840.02,917.1 273 60.00 3.566 0.166 4.4 09/29/09 41,119,370.3 280.1 1,840.02,949.8 275 60.00 4.001 0.189 4.3 09/29/09 40,899,166.4 280.9 1,840.02,934.1 276 60.00 3.827 0.180 3.9 09/29/09 41,352,983.3 280.51,840.02,966.6 279 60.00 3.740 0.177 4.1 09/29/09 41,570,980.6 281.3 1,840.03,004.9 281 60.00 3.367 0.162 4.4 09/29/09 41,386,438.7 281.1 1,840.02,969.0 279 60.00 3.566 0.169 4.5 09/29/09 41,359,987.0 280.9 1,840.02,967.1 280 60.00 3.827 0.182 4.5 09/29/09 41,513,587.3 280.2 1,840.02,978.2 280 60.00 3.914 0.186 09/29/09 41,305,401.1 279.9 1,840.02,963.2 278 60.00 3.914 0.185

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 5.9 6.0 10/02/09 41,510,351.1 279.9 1,840.02,887.7 277 60.00 5.338 0.246 5.9 10/02/09 42,149,626.2 279.9 1,840.02,932.2 281 60.00 5.417 0.254 6.2 10/02/09 42,465,869.8 279.8 1,840.02,954.2 282 60.00 5.275 0.249 6.1 10/02/09 41,532,510.7 279.1 1,840.02,866.7 275 60.00 5.624 0.259 4.1 10/02/09 36,840,126.1 270.8 1,840.02,622.8 238 60.00 5.360 0.224 5.3 10/02/09 28,402,270.9 264.6 1,840.0 1,898.6 170 60.00 3.842 0.117 5.6 10/02/09 26,790,360.7 266.51,840.0 1,732.6 161 60.00 5.084 0.141 5.8 10/02/09 29,000,274.7 267.0 1,840.0 1,844.0 175 60.00 5.496 0.163 5.8 10/02/09 29,350,067.2 266.8 1,840.0 1,946.0 180 60.00 5.432 0.169 5.9 10/02/09 28,900,162.1 267.2 1,840.0 1,916.2 179 60.00 5.401 0.166 5.1 10/01/09 29,132,702.1 266.6 1,840.0 1,915.8 178 60.00 5.612 0.171 5.0 10/01/09 27,125,418.5 268.3 1,840.0 1,842.7 168 60.00 4.693 0.138 4.8 10/01/09 30,302,761.9 270.4 1,840.02,075.1 189 60.00 4.534 0.151 5.3 10/01/09 33,771,633.3 276.4 1,840.02,312.6 220 60.00 4.362 0.162 5.5 10/01/09 39,476,935.2 283.3 1,840.02,810.6 267 60.00 4.618 0.208 5.4 10/01/09 40,693,122.5 284.0 1,840.02,897.2 274 60.00 4.828 0.224 5.2 10/01/09 40,827,222.9 282.2 1,840.02,906.7 275 60.00 4.703 0.219 5.3 10/01/09 38,820,902.8 279.2 1,840.02,721.7 260 60.00 4.587 0.200 5.3 10/01/09 39,392,996.1 280.9 1,840.02,783.2 266 60.00 4.660 0.208 4.7 10/01/09 40,988,681.6 281.4 1,840.02,918.2 279 60.00 4.632 0.217 4.8 10/01/09 40,810,970.4 279.2 1,840.02,905.6 276 60.00 4.150 0.193 5.1 10/01/09 40,041,338.2 280.4 1,840.02,850.7 268 60.00 4.228 0.193 4.9 10/01/09 40,328,246.2 280.0 1,840.02,871.2 270 60.00 4.438 0.204 5.1 10/01/09 39,555,506.9 279.1 1,840.02,816.2 264 60.00 4.282 0.193 5.0 10/01/09 36,989,296.2 274.1 1,840.02,593.3 242 60.00 4.519 0.188 5.4 10/01/09 35,364,978.1 275.8 1,840.02,479.4 233 60.00 4.429 0.175 4.4 10/01/09 39,855,587.7 276.8 1,840.02,859.2 268 60.00 4.738 0.216 2.6 10/01/09 35,998,215.3 268.51,840.02,562.9 233 60.00 3.826 0.157 3.3 10/01/09 28,312,067.7 263.6 1,840.0 1,923.4 173 60.00 2.416 0.074 2.9 10/01/09 26,481,541.4 264.4 1,840.0 1,755.9 163 60.00 3.071 0.086 2.9 10/01/09 27,868,976.1 263.2 1,840.0 1,832.7 168 60.00 2.757 0.081 3.4 10/01/09 25,716,844.4 263.4 1,840.0 1,607.3 155 60.00 2.883 0.074 3.2 10/01/09 27,194,795.0 263.6 1,840.0 1,788.4 164 60.00 3.214 0.092 3.7 10/01/09 25,728,437.2 266.0 1,840.0 1,663.9 157 60.00 3.097 0.082 4.1 09/30/09 29,943,861.4 269.9 1,840.02,083.1 194 60.00 3.319 0.111 4.2 09/30/09 31,744,352.6 269.8 1,840.02,208.3 206 60.00 3.678 0.130 09/30/09 31,583,782.8 272.3 1,840.02,180.0 207 60.00 3.797 0.132

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 4.1 3.9 10/03/09 29,514,867.7 267.51,840.02,021.1 189 60.00 3.693 0.120 4.8 10/03/09 33,796,992.0 272.3 1,840.02,369.5 226 60.00 3.513 0.133 4.7 10/03/09 37,621,119.8 275.7 1,840.02,637.6 251 60.00 4.306 0.182 4.2 10/03/09 40,785,419.7 277.7 1,840.02,881.5 274 60.00 4.193 0.193 4.1 10/03/09 38,431,039.3 275.6 1,840.02,694.3 254 60.00 3.692 0.160 4.4 10/03/09 34,327,874.4 271.4 1,840.02,388.0 220 60.00 3.657 0.140 5.0 10/03/09 33,190,954.1 272.2 1,840.02,308.9 219 60.00 3.974 0.147 4.3 10/03/09 35,568,203.3 272.7 1,840.02,474.3 233 60.00 4.460 0.177 3.4 10/03/09 32,540,571.7 270.2 1,840.02,281.4 214 60.00 3.817 0.140 4.1 10/03/09 33,259,661.3 270.9 1,840.02,313.7 214 60.00 3.083 0.114 4.3 10/03/09 34,600,154.2 273.2 1,840.02,388.2 224 60.00 3.731 0.143 4.3 10/03/09 36,643,128.7 275.1 1,840.02,569.0 240 60.00 3.777 0.156 4.3 10/03/09 36,101,160.2 273.7 1,840.02,550.6 238 60.00 3.823 0.156 5.4 10/03/09 35,305,997.2 273.8 1,840.02,475.3 233 60.00 3.805 0.150 4.9 10/03/09 38,057,917.4 274.9 1,840.02,668.2 252 60.00 4.857 0.207 4.0 10/03/09 37,821,226.2 271.7 1,840.02,631.0 245 60.00 4.360 0.183 4.6 10/03/09 32,564,280.0 268.2 1,840.02,194.5 208 60.00 3.749 0.132 3.4 10/03/09 33,390,485.8 267.51,840.02,250.2 213 60.00 4.221 0.152 3.3 10/03/09 29,824,001.1 264.51,840.0 1,993.7 186 60.00 3.198 0.102 3.6 10/03/09 29,196,073.7 264.9 1,840.0 1,904.1 179 60.00 3.210 0.098 4.0 10/03/09 29,990,235.8 265.51,840.0 1,939.6 181 60.00 3.497 0.108 4.1 10/03/09 29,456,468.8 265.6 1,840.0 1,953.1 178 60.00 3.740 0.117 3.3 10/03/09 29,029,066.8 265.8 1,840.0 1,956.3 182 60.00 3.782 0.118 4.0 10/02/09 29,002,862.4 266.4 1,840.0 1,970.3 182 60.00 3.039 0.095 4.9 10/02/09 31,498,201.8 270.9 1,840.02,156.9 207 60.00 3.630 0.125 4.9 10/02/09 37,746,428.6 275.0 1,840.02,666.8 252 60.00 4.301 0.183 5.1 10/02/09 37,938,307.3 277.0 1,840.02,659.8 254 60.00 4.377 0.186 5.0 10/02/09 39,581,450.2 278.9 1,840.02,818.0 270 60.00 4.440 0.200 5.8 10/02/09 39,991,071.5 280.8 1,840.02,890.7 275 60.00 4.312 0.199 5.8 10/02/09 39,512,791.1 279.0 1,840.02,856.1 269 60.00 5.023 0.229 5.9 10/02/09 40,431,394.6 278.1 1,840.02,768.6 269 60.00 5.315 0.235 5.8 10/02/09 41,324,545.6 277.51,840.02,829.9 276 60.00 5.327 0.241 5.8 10/02/09 40,935,265.2 278.9 1,840.02,803.2 273 60.00 5.292 0.237 6.1 10/02/09 41,261,557.7 279.0 1,840.02,848.0 275 60.00 5.254 0.239 6.3 10/02/09 41,433,091.4 280.0 1,840.02,859.8 276 60.00 5.479 0.251 6.1 10/02/09 41,411,783.5 280.2 1,840.02,880.8 278 60.00 5.601 0.259 10/02/09 41,334,471.9 279.0 1,840.02,920.3 279 60.00 5.392 0.251

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 4.7 5.1 10/05/09 40,963,192.6 278.0 1,840.02,916.4 278 60.00 4.160 0.194 4.9 10/05/09 41,159,282.6 278.3 1,840.02,908.0 277 60.00 4.457 0.208 4.8 10/05/09 40,726,792.2 277.8 1,840.02,877.5 273 60.00 4.319 0.199 4.6 10/05/09 40,863,955.4 278.8 1,840.02,887.1 275 60.00 4.221 0.195 4.6 10/05/09 41,110,710.4 277.8 1,840.02,949.3 280 60.00 3.986 0.187 4.7 10/05/09 40,364,722.5 276.3 1,840.02,895.8 274 60.00 3.960 0.183 4.1 10/05/09 40,672,459.3 275.7 1,840.02,917.8 276 60.00 4.127 0.193 3.5 10/05/09 36,773,242.0 270.4 1,840.02,618.1 238 60.00 3.567 0.149 3.1 10/05/09 31,826,283.6 267.3 1,840.02,231.3 201 60.00 3.104 0.111 2.7 10/05/09 30,402,170.9 266.1 1,840.02,081.9 191 60.00 2.870 0.095 2.6 10/05/09 28,962,454.2 264.8 1,840.0 1,967.5 182 60.00 2.485 0.078 2.4 10/05/09 29,125,584.7 264.6 1,840.02,026.2 186 60.00 2.304 0.074 3.5 10/04/09 28,231,541.1 266.3 1,840.0 1,948.6 182 60.00 2.128 0.066 3.8 10/04/09 30,088,665.4 268.0 1,840.02,093.1 190 60.00 3.175 0.106 4.1 10/04/09 31,636,298.3 270.6 1,840.02,166.4 202 60.00 3.487 0.121 4.4 10/04/09 35,742,121.6 275.6 1,840.02,505.8 238 60.00 3.647 0.146 4.2 10/04/09 39,523,220.2 277.0 1,840.02,813.9 267 60.00 3.833 0.173 4.4 10/04/09 39,069,055.6 276.0 1,840.02,802.8 264 60.00 3.610 0.162 4.3 10/04/09 36,663,654.8 273.2 1,840.02,570.5 243 60.00 3.951 0.163 4.1 10/04/09 36,776,211.1 272.7 1,840.02,578.3 241 60.00 3.821 0.157 4.2 10/04/09 35,821,720.4 271.6 1,840.02,472.5 230 60.00 3.686 0.146 3.8 10/04/09 35,163,634.4 272.4 1,840.02,408.0 227 60.00 3.792 0.146 3.5 10/04/09 35,083,485.1 270.4 1,840.02,402.4 224 60.00 3.417 0.132 3.9 10/04/09 32,656,426.6 269.3 1,840.02,236.2 212 60.00 3.182 0.114 4.3 10/04/09 34,678,368.7 272.6 1,840.02,412.4 226 60.00 3.522 0.135 3.5 10/04/09 35,687,646.7 272.2 1,840.02,502.0 231 60.00 3.860 0.154 4.2 10/04/09 34,257,860.8 271.7 1,840.02,383.2 221 60.00 3.159 0.120 4.8 10/04/09 35,678,410.2 274.51,840.02,481.9 234 60.00 3.786 0.150 4.1 10/04/09 37,796,121.8 272.4 1,840.02,670.4 247 60.00 4.295 0.183 3.5 10/04/09 32,589,193.6 267.8 1,840.02,249.3 210 60.00 3.663 0.132 3.7 10/04/09 31,012,704.1 265.2 1,840.02,140.6 197 60.00 3.193 0.109 3.3 10/04/09 28,502,825.9 263.6 1,840.0 1,936.3 178 60.00 3.383 0.105 3.3 10/04/09 27,499,702.2 263.0 1,840.0 1,853.3 172 60.00 3.036 0.090 3.3 10/04/09 28,183,919.6 264.1 1,840.0 1,899.4 174 60.00 3.050 0.093 3.3 10/04/09 28,193,002.9 264.6 1,840.0 1,915.3 174 60.00 3.024 0.093 3.3 10/04/09 28,494,837.1 265.8 1,840.0 1,904.8 175 60.00 3.077 0.094 10/03/09 29,131,636.1 266.4 1,840.0 1,963.2 180 60.00 3.027 0.095

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 3.8 3.1 10/07/09 26,829,224.7 265.1 1,840.0 1,837.2 168 60.00 3.435 0.101 3.8 10/06/09 27,210,913.9 264.3 1,840.0 1,863.4 169 60.00 2.843 0.085 4.2 10/06/09 25,163,666.0 265.51,840.0 1,682.2 153 60.00 3.524 0.095 4.7 10/06/09 28,586,679.2 269.9 1,840.0 1,879.9 181 60.00 3.946 0.119 5.6 10/06/09 32,420,430.4 275.1 1,840.02,202.4 210 60.00 4.285 0.151 5.8 10/06/09 40,302,104.0 280.6 1,840.02,803.6 270 60.00 5.074 0.227 4.1 10/06/09 39,906,078.9 275.51,840.02,797.8 266 60.00 5.185 0.232 4.0 10/06/09 30,645,858.4 267.3 1,840.02,115.2 198 60.00 3.717 0.126 3.9 10/06/09 33,940,383.2 273.0 1,840.02,287.3 219 60.00 3.722 0.136 4.1 10/06/09 37,107,890.6 273.3 1,840.02,541.1 240 60.00 3.591 0.146 4.1 10/06/09 38,963,252.8 276.1 1,840.02,710.5 258 60.00 3.707 0.160 4.3 10/06/09 38,557,389.6 276.3 1,840.02,682.2 256 60.00 3.629 0.156 4.7 10/06/09 40,469,683.5 278.3 1,840.02,837.3 272 60.00 3.806 0.173 4.5 10/06/09 41,382,995.6 278.3 1,840.02,901.3 277 60.00 4.150 0.193 3.6 10/06/09 41,264,721.4 277.6 1,840.02,915.5 277 60.00 3.994 0.186 2.9 10/06/09 40,551,605.4 276.7 1,840.02,865.1 272 60.00 3.142 0.144 3.3 10/06/09 40,304,428.7 277.0 1,840.02,869.5 272 60.00 2.550 0.117 3.9 10/06/09 40,546,047.7 277.3 1,840.02,908.7 274 60.00 2.875 0.134 2.7 10/06/09 40,603,466.3 275.2 1,840.02,912.8 272 60.00 3.355 0.157 2.8 10/06/09 33,713,657.7 264.8 1,840.02,400.3 216 60.00 2.331 0.089 2.5 10/06/09 25,986,269.5 260.7 1,840.0 1,751.2 160 60.00 2.571 0.072 2.8 10/06/09 25,198,619.4 261.7 1,840.0 1,670.8 154 60.00 2.304 0.062 2.8 10/06/09 26,000,093.5 263.2 1,840.0 1,709.8 157 60.00 2.669 0.073 2.8 10/06/09 27,600,570.5 264.2 1,840.0 1,830.1 167 60.00 2.651 0.077 3.2 10/06/09 28,073,421.7 264.3 1,840.0 1,861.4 171 60.00 2.636 0.079 3.7 10/05/09 25,369,958.5 263.4 1,840.0 1,737.3 156 60.00 2.889 0.080 4.1 10/05/09 26,376,741.0 266.7 1,840.0 1,777.6 168 60.00 3.414 0.097 4.5 10/05/09 31,595,081.6 270.9 1,840.02,163.6 206 60.00 3.723 0.129 4.0 10/05/09 38,678,066.1 277.1 1,840.02,711.7 255 60.00 3.963 0.172 4.2 10/05/09 37,989,650.4 274.6 1,840.02,663.4 249 60.00 3.579 0.153 4.0 10/05/09 39,561,786.6 278.0 1,840.02,795.1 266 60.00 3.667 0.164 4.6 10/05/09 39,313,503.5 275.8 1,840.02,777.6 263 60.00 3.570 0.158 4.4 10/05/09 39,370,417.0 276.1 1,840.02,781.6 265 60.00 4.033 0.179 4.4 10/05/09 39,492,154.3 276.3 1,840.02,768.7 263 60.00 3.887 0.173 4.6 10/05/09 39,240,170.6 276.0 1,840.02,772.4 260 60.00 3.907 0.173 4.7 10/05/09 39,822,651.9 276.8 1,840.02,813.6 265 60.00 4.040 0.181 10/05/09 40,677,208.5 277.51,840.02,873.9 275 60.00 4.151 0.191

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 4.8 4.5 10/08/09 41,308,787.2 279.2 1,840.02,918.6 278 60.00 4.248 0.198 4.9 10/08/09 41,152,739.8 278.9 1,840.02,885.2 278 60.00 4.005 0.185 5.2 10/08/09 41,457,492.6 278.51,840.02,906.5 278 60.00 4.346 0.201 5.3 10/08/09 41,207,808.2 278.4 1,840.02,889.0 278 60.00 4.594 0.213 5.3 10/08/09 41,298,892.3 279.2 1,840.02,917.9 279 60.00 4.650 0.218 5.3 10/08/09 41,685,133.8 279.3 1,840.02,945.1 281 60.00 4.703 0.221 4.3 10/08/09 40,228,482.7 276.2 1,840.02,820.3 267 60.00 4.673 0.211 3.8 10/08/09 35,507,684.4 270.8 1,840.02,489.4 228 60.00 3.816 0.152 3.3 10/08/09 27,954,595.8 264.9 1,840.0 1,975.1 170 60.00 3.362 0.106 3.5 10/08/09 24,804,333.8 263.9 1,840.0 1,698.5 149 60.00 3.054 0.083 3.8 10/08/09 24,788,106.1 263.51,840.0 1,670.5 149 60.00 3.255 0.087 3.5 10/08/09 24,575,205.1 262.8 1,840.0 1,629.4 149 60.00 3.562 0.093 3.5 10/08/09 24,522,437.7 262.6 1,840.0 1,652.6 149 60.00 3.208 0.085 3.1 10/08/09 24,400,723.0 262.7 1,840.0 1,657.7 149 60.00 3.178 0.084 4.9 10/07/09 23,580,504.7 265.8 1,840.0 1,563.5 144 60.00 2.940 0.074 5.3 10/07/09 31,980,650.9 274.8 1,840.02,242.1 215 60.00 4.403 0.158 5.4 10/07/09 37,835,843.3 277.4 1,840.02,714.3 252 60.00 4.591 0.200 5.1 10/07/09 38,689,535.4 279.4 1,840.02,796.6 260 60.00 4.641 0.207 4.5 10/07/09 40,050,288.0 279.8 1,840.02,873.2 269 60.00 4.402 0.203 4.0 10/07/09 38,667,641.2 277.1 1,840.02,774.0 258 60.00 3.912 0.174 3.1 10/07/09 36,243,520.6 272.51,840.02,560.7 240 60.00 3.520 0.145 3.1 10/07/09 33,793,890.2 269.7 1,840.02,350.9 217 60.00 2.728 0.103 2.7 10/07/09 31,943,879.1 269.7 1,840.02,204.8 204 60.00 2.825 0.100 3.2 10/07/09 30,931,058.0 270.4 1,840.02,118.1 198 60.00 2.439 0.082 1.9 10/07/09 33,452,583.4 273.6 1,840.02,327.2 216 60.00 2.883 0.107 4.6 10/07/09 38,058,804.0 277.1 1,840.02,709.6 254 60.00 1.653 0.072 4.2 10/07/09 40,324,708.0 279.0 1,840.02,914.8 273 60.00 3.934 0.183 4.2 10/07/09 41,062,016.0 278.51,840.02,945.8 277 60.00 3.659 0.172 4.5 10/07/09 41,854,696.4 280.1 1,840.03,002.6 281 60.00 3.624 0.173 4.7 10/07/09 41,271,450.7 279.51,840.02,938.3 275 60.00 3.948 0.185 5.1 10/07/09 40,858,086.8 279.3 1,840.02,931.1 271 60.00 4.135 0.193 3.6 10/07/09 38,456,225.0 273.3 1,840.02,717.0 248 60.00 4.459 0.194 3.6 10/07/09 29,813,611.6 266.1 1,840.0 1,993.0 182 60.00 3.304 0.106 4.2 10/07/09 28,063,750.0 265.7 1,840.0 1,906.5 172 60.00 3.296 0.100 3.8 10/07/09 27,930,930.6 267.2 1,840.0 1,821.6 170 60.00 4.041 0.118 4.1 10/07/09 28,023,725.7 266.7 1,840.0 1,812.4 171 60.00 3.622 0.105 10/07/09 28,397,200.4 265.9 1,840.0 1,882.8 176 60.00 3.844 0.116

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 2.7 2.5 10/10/09 27,400,751.2 264.0 1,840.0 1,950.8 170 60.00 2.401 0.075 2.5 10/10/09 25,626,259.0 263.0 1,840.0 1,768.8 159 60.00 2.247 0.064 2.2 10/10/09 25,938,729.2 262.51,840.0 1,832.6 163 60.00 2.197 0.064 2.6 10/09/09 25,434,379.6 263.8 1,840.0 1,783.1 161 60.00 1.998 0.057 2.9 10/09/09 26,943,062.1 266.0 1,840.0 1,859.7 173 60.00 2.356 0.070 4.0 10/09/09 33,249,208.4 273.2 1,840.02,313.0 225 60.00 2.564 0.095 3.8 10/09/09 40,159,659.0 275.8 1,840.02,902.9 274 60.00 3.489 0.162 4.2 10/09/09 41,021,961.6 276.9 1,840.02,965.2 280 60.00 3.260 0.154 4.7 10/09/09 40,893,108.2 277.4 1,840.02,955.9 278 60.00 3.644 0.172 4.5 10/09/09 41,336,758.1 277.3 1,840.02,987.9 280 60.00 4.048 0.193 4.4 10/09/09 40,716,893.3 276.4 1,840.02,898.9 270 60.00 3.929 0.183 4.8 10/09/09 38,006,117.8 274.0 1,840.02,726.5 251 60.00 3.821 0.166 5.0 10/09/09 39,320,613.8 276.9 1,840.02,820.9 263 60.00 4.207 0.189 4.5 10/09/09 39,910,238.5 276.1 1,840.02,863.1 267 60.00 4.314 0.198 4.7 10/09/09 40,017,927.4 277.51,840.02,892.6 271 60.00 3.924 0.181 4.6 10/09/09 40,213,611.0 278.7 1,840.02,906.8 272 60.00 4.068 0.189 4.6 10/09/09 41,363,919.6 279.9 1,840.02,989.9 283 60.00 3.960 0.189 5.0 10/09/09 41,546,377.8 279.8 1,840.02,935.3 282 60.00 4.040 0.190 5.0 10/09/09 41,238,136.0 278.7 1,840.02,958.4 281 60.00 4.343 0.205 4.8 10/09/09 41,723,735.3 278.7 1,840.02,947.9 280 60.00 4.434 0.209 4.5 10/09/09 40,479,165.4 277.3 1,840.02,881.9 274 60.00 4.235 0.195 3.3 10/09/09 36,546,667.9 270.2 1,840.02,562.3 237 60.00 3.982 0.163 3.6 10/09/09 30,561,452.3 267.7 1,840.02,076.2 194 60.00 3.006 0.100 3.1 10/09/09 30,112,539.0 266.51,840.02,045.7 188 60.00 3.314 0.109 3.5 10/09/09 27,421,626.5 265.51,840.0 1,803.3 168 60.00 2.973 0.086 3.5 10/09/09 27,150,554.4 263.9 1,840.0 1,829.7 169 60.00 3.235 0.095 3.3 10/09/09 25,899,712.3 264.51,840.0 1,717.3 161 60.00 3.291 0.090 4.0 10/08/09 27,315,540.0 264.0 1,840.0 1,840.9 171 60.00 3.091 0.091 4.6 10/08/09 25,882,507.1 266.6 1,840.0 1,716.2 164 60.00 3.748 0.103 5.4 10/08/09 31,970,606.2 273.9 1,840.02,189.3 208 60.00 4.176 0.146 4.9 10/08/09 38,141,366.1 279.51,840.02,715.5 254 60.00 4.694 0.204 4.9 10/08/09 41,512,454.9 281.1 1,840.03,000.6 281 60.00 4.201 0.201 5.0 10/08/09 41,413,704.0 282.0 1,840.02,971.0 282 60.00 4.285 0.204 5.0 10/08/09 41,732,774.0 281.51,840.02,971.2 282 60.00 4.372 0.208 4.8 10/08/09 41,270,484.1 281.0 1,840.02,871.0 278 60.00 4.446 0.204 4.8 10/08/09 41,232,990.1 280.1 1,840.02,890.8 278 60.00 4.236 0.196 10/08/09 40,932,670.5 279.2 1,840.02,914.3 278 60.00 4.248 0.197

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 2.6 2.3 10/11/09 36,898,545.7 268.9 1,840.02,627.0 241 60.00 2.254 0.095 2.6 10/11/09 33,400,360.7 266.7 1,840.02,359.8 217 60.00 2.065 0.078 3.4 10/11/09 34,082,982.4 267.6 1,840.02,389.5 219 60.00 2.298 0.088 3.8 10/11/09 33,404,659.8 270.51,840.02,323.8 217 60.00 3.025 0.112 3.7 10/11/09 40,365,280.5 273.0 1,840.02,851.9 271 60.00 3.403 0.155 3.9 10/11/09 39,733,250.1 274.2 1,840.02,807.2 266 60.00 3.281 0.148 3.6 10/11/09 39,659,972.4 274.4 1,840.02,823.6 266 60.00 3.408 0.154 3.9 10/11/09 40,300,346.9 274.0 1,840.02,869.2 271 60.00 3.161 0.146 3.5 10/11/09 39,453,728.8 272.9 1,840.02,830.4 264 60.00 3.420 0.154 2.7 10/11/09 36,082,037.3 268.8 1,840.02,529.7 235 60.00 3.104 0.126 3.2 10/11/09 31,900,082.5 266.0 1,840.02,253.8 204 60.00 2.390 0.086 2.9 10/11/09 28,020,740.8 263.8 1,840.0 1,979.7 181 60.00 2.816 0.089 3.0 10/11/09 28,617,056.3 263.0 1,840.02,006.3 184 60.00 2.580 0.083 3.1 10/11/09 27,727,954.0 263.1 1,840.0 1,928.9 177 60.00 2.640 0.082 3.3 10/11/09 27,381,092.8 263.6 1,840.0 1,919.6 175 60.00 2.725 0.084 3.2 10/11/09 27,605,282.2 264.2 1,840.0 1,935.4 179 60.00 2.896 0.090 3.3 10/10/09 28,195,079.4 265.0 1,840.0 1,961.4 182 60.00 2.862 0.090 3.7 10/10/09 32,155,845.9 268.8 1,840.02,236.9 211 60.00 2.911 0.104 3.8 10/10/09 37,015,733.1 272.6 1,840.02,615.3 246 60.00 3.292 0.138 3.8 10/10/09 37,558,098.0 274.0 1,840.02,694.4 254 60.00 3.313 0.143 3.8 10/10/09 40,255,686.2 274.7 1,840.02,931.7 273 60.00 3.254 0.152 3.1 10/10/09 38,140,592.9 274.7 1,840.02,736.2 254 60.00 3.278 0.143 3.2 10/10/09 36,319,038.5 269.2 1,840.02,645.0 238 60.00 2.631 0.111 3.0 10/10/09 32,009,340.9 266.7 1,840.02,296.3 209 60.00 2.745 0.101 2.8 10/10/09 31,191,596.8 266.0 1,840.02,220.7 201 60.00 2.608 0.093 3.1 10/10/09 28,640,153.3 272.4 1,840.02,023.5 183 60.00 2.459 0.080 3.2 10/10/09 28,343,630.4 268.8 1,840.02,018.0 181 60.00 2.708 0.088 3.4 10/10/09 29,355,012.6 266.8 1,840.02,058.0 187 60.00 2.835 0.093 4.1 10/10/09 30,257,812.4 269.1 1,840.02,104.9 195 60.00 3.077 0.104 3.1 10/10/09 35,834,303.2 270.4 1,840.02,473.3 235 60.00 3.728 0.148 3.5 10/10/09 31,720,333.4 269.2 1,840.02,275.6 211 60.00 2.713 0.099 2.9 10/10/09 37,263,206.7 273.1 1,840.02,673.2 250 60.00 3.065 0.131 3.1 10/10/09 36,555,991.1 271.0 1,840.02,662.2 242 60.00 2.499 0.107 2.7 10/10/09 33,636,747.7 268.2 1,840.02,394.8 218 60.00 2.702 0.104 2.9 10/10/09 30,804,529.8 265.7 1,840.02,109.5 197 60.00 2.459 0.083 2.4 10/10/09 28,525,632.7 265.1 1,840.0 1,999.9 181 60.00 2.568 0.082 10/10/09 26,997,708.9 265.0 1,840.0 1,922.1 171 60.00 2.121 0.065

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 3.7 3.8 10/13/09 36,637,923.3 271.6 1,840.02,648.3 245 60.00 3.171 0.134 4.2 10/13/09 38,520,686.5 275.2 1,840.02,763.5 261 60.00 3.259 0.144 4.3 10/13/09 40,331,263.7 276.3 1,840.02,893.3 272 60.00 3.611 0.167 3.7 10/13/09 40,735,909.1 275.7 1,840.02,944.5 277 60.00 3.686 0.173 4.1 10/13/09 37,483,395.9 273.3 1,840.02,668.6 251 60.00 3.223 0.138 4.0 10/12/09 39,893,223.3 275.9 1,840.02,883.6 273 60.00 3.495 0.161 3.8 10/12/09 39,489,177.5 275.2 1,840.02,854.4 270 60.00 3.441 0.157 3.9 10/12/09 41,031,459.4 276.7 1,840.02,965.8 280 60.00 3.313 0.157 3.3 10/12/09 40,678,908.9 276.9 1,840.02,940.4 277 60.00 3.350 0.157 3.3 10/12/09 40,888,162.2 276.9 1,840.02,933.3 277 60.00 2.844 0.133 3.3 10/12/09 39,652,202.8 276.4 1,840.02,866.2 270 60.00 2.888 0.132 3.2 10/12/09 40,073,436.1 276.4 1,840.02,918.4 273 60.00 2.817 0.131 3.2 10/12/09 40,848,875.6 277.3 1,840.02,974.9 280 60.00 2.753 0.131 3.3 10/12/09 41,069,051.4 277.8 1,840.02,990.9 281 60.00 2.783 0.133 3.8 10/12/09 40,264,439.1 279.9 1,840.02,932.3 276 60.00 2.869 0.134 4.0 10/12/09 40,667,405.8 292.6 1,840.02,983.7 280 60.00 3.224 0.153 3.9 10/12/09 40,918,806.5 293.51,840.03,002.2 281 60.00 3.407 0.164 3.7 10/12/09 40,271,872.8 290.9 1,840.02,954.7 275 60.00 3.293 0.155 4.2 10/12/09 40,637,527.9 289.0 1,840.02,959.5 278 60.00 3.211 0.152 4.1 10/12/09 40,606,918.2 286.3 1,840.02,957.2 277 60.00 3.561 0.169 4.0 10/12/09 40,808,956.3 284.3 1,840.02,994.1 281 60.00 3.526 0.168 3.8 10/12/09 41,128,679.9 282.4 1,840.02,995.3 284 60.00 3.454 0.166 3.9 10/12/09 40,997,187.1 281.7 1,840.03,007.9 282 60.00 3.207 0.155 3.2 10/12/09 39,653,261.5 277.7 1,840.02,844.7 268 60.00 3.382 0.154 2.7 10/12/09 36,466,195.7 271.8 1,840.02,556.6 240 60.00 2.845 0.117 2.4 10/12/09 32,422,191.9 267.3 1,840.02,325.9 212 60.00 2.322 0.087 2.6 10/12/09 28,833,377.0 265.3 1,840.02,052.8 187 60.00 2.103 0.069 2.6 10/12/09 28,538,490.3 266.0 1,840.02,062.8 185 60.00 2.235 0.074 2.8 10/12/09 28,657,196.2 266.9 1,840.02,055.8 184 60.00 2.252 0.074 3.0 10/11/09 29,441,134.3 268.9 1,840.02,112.1 190 60.00 2.408 0.081 3.4 10/11/09 32,574,104.3 272.3 1,840.02,283.7 218 60.00 2.685 0.098 3.0 10/11/09 39,747,169.5 275.6 1,840.02,786.6 268 60.00 2.989 0.133 3.6 10/11/09 39,512,941.6 274.7 1,840.02,791.7 267 60.00 2.681 0.120 3.4 10/11/09 41,016,294.5 276.3 1,840.02,920.2 278 60.00 3.153 0.148 3.2 10/11/09 40,848,366.6 276.51,840.02,930.4 279 60.00 2.977 0.140 3.1 10/11/09 40,165,824.8 274.3 1,840.02,881.5 271 60.00 2.832 0.130 10/11/09 37,042,790.3 270.9 1,840.02,617.2 245 60.00 2.718 0.113

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 4.6 4.4 10/14/09 42,238,095.3 279.9 1,840.03,007.2 281 60.00 4.008 0.192 4.5 10/14/09 40,867,263.1 277.9 1,840.02,931.8 275 60.00 3.815 0.179 4.5 10/14/09 40,859,511.1 278.4 1,840.02,909.1 274 60.00 3.946 0.183 4.4 10/14/09 41,685,875.4 278.8 1,840.02,967.9 280 60.00 3.952 0.188 4.7 10/14/09 41,896,631.3 279.3 1,840.02,982.9 282 60.00 3.841 0.183 4.3 10/14/09 41,704,801.8 278.6 1,840.02,991.9 282 60.00 4.076 0.195 4.3 10/14/09 41,529,592.2 278.6 1,840.02,979.3 279 60.00 3.785 0.180 4.3 10/14/09 41,786,804.7 278.7 1,840.02,997.8 280 60.00 3.781 0.181 4.5 10/14/09 41,745,744.9 278.6 1,840.02,994.8 280 60.00 3.776 0.181 4.8 10/14/09 41,282,655.2 279.0 1,840.02,939.2 277 60.00 3.894 0.184 4.7 10/14/09 41,736,283.6 277.9 1,840.03,016.8 282 60.00 4.163 0.200 4.3 10/14/09 41,203,985.5 276.4 1,840.02,955.9 276 60.00 4.098 0.193 3.6 10/14/09 38,497,810.8 272.4 1,840.02,803.7 254 60.00 3.701 0.165 3.9 10/14/09 31,541,762.2 266.8 1,840.02,245.7 200 60.00 3.109 0.112 3.8 10/14/09 30,162,070.0 268.3 1,840.02,081.8 193 60.00 3.482 0.116 3.4 10/14/09 31,537,552.8 267.7 1,840.02,176.8 204 60.00 3.459 0.121 3.4 10/14/09 32,588,334.8 268.3 1,840.02,196.1 205 60.00 3.198 0.112 3.1 10/14/09 33,194,600.1 269.4 1,840.02,291.2 212 60.00 3.109 0.114 3.5 10/13/09 32,127,528.2 269.0 1,840.02,304.8 204 60.00 2.665 0.098 4.1 10/13/09 33,696,354.9 272.7 1,840.02,380.7 221 60.00 3.102 0.118 3.8 10/13/09 39,744,582.1 277.3 1,840.02,851.3 267 60.00 3.564 0.163 3.5 10/13/09 40,938,515.2 278.4 1,840.02,981.4 277 60.00 3.261 0.156 3.5 10/13/09 40,457,348.0 278.7 1,840.02,946.3 273 60.00 3.000 0.141 3.8 10/13/09 40,812,226.6 278.9 1,840.02,972.2 275 60.00 3.000 0.142 3.5 10/13/09 40,981,935.6 279.6 1,840.02,984.6 278 60.00 3.283 0.156 3.5 10/13/09 40,719,011.1 278.3 1,840.02,965.4 276 60.00 3.017 0.143 3.3 10/13/09 40,141,578.2 277.4 1,840.02,923.4 271 60.00 3.000 0.140 3.1 10/13/09 39,877,771.9 276.6 1,840.02,904.2 269 60.00 2.837 0.132 2.8 10/13/09 40,554,617.5 276.8 1,840.02,975.5 274 60.00 2.642 0.126 2.8 10/13/09 41,283,116.9 278.1 1,840.03,028.9 279 60.00 2.391 0.116 3.2 10/13/09 41,244,667.7 278.2 1,840.03,003.7 280 60.00 2.410 0.116 3.9 10/13/09 41,303,446.5 279.3 1,840.03,007.9 281 60.00 2.744 0.132 4.3 10/13/09 40,915,169.0 278.6 1,840.03,001.9 279 60.00 3.318 0.159 4.2 10/13/09 40,779,654.2 278.3 1,840.02,992.0 279 60.00 3.621 0.174 4.3 10/13/09 40,674,562.4 276.9 1,840.02,984.3 276 60.00 3.583 0.171 3.4 10/13/09 40,138,866.9 276.1 1,840.02,923.2 274 60.00 3.675 0.172 10/13/09 39,228,141.1 273.4 1,840.02,835.5 266 60.00 2.944 0.134

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C ST ST 03:00 ST ST 04:00 ST ST C 05:00 C ST ST C 06:00 ST ST 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 4.4 4.2 10/16/09 40,405,092.9 283.6 1,840.02,942.5 274 60.00 3.794 0.178 4.0 10/16/09 40,556,221.8 281.3 1,840.02,931.5 275 60.00 3.610 0.169 4.1 10/16/09 38,578,027.5 279.2 1,840.02,725.6 257 60.00 3.568 0.155 4.1 10/16/09 38,601,067.1 279.3 1,840.02,727.2 257 60.00 3.670 0.160 3.9 10/16/09 36,723,845.6 276.2 1,840.02,534.8 245 60.00 3.661 0.149 3.9 10/16/09 36,848,328.7 276.51,840.02,583.4 244 60.00 3.441 0.142 3.7 10/16/09 37,305,549.9 278.1 1,840.02,635.8 249 60.00 3.409 0.144 3.4 10/15/09 40,837,324.7 281.2 1,840.02,929.6 279 60.00 3.212 0.151 3.7 10/15/09 39,441,920.9 279.2 1,840.02,808.1 266 60.00 2.953 0.133 3.6 10/15/09 40,913,870.9 281.7 1,840.02,957.4 282 60.00 3.172 0.150 3.8 10/15/09 40,825,353.0 280.51,840.02,928.8 279 60.00 3.121 0.146 4.0 10/15/09 40,720,019.5 281.1 1,840.02,921.2 278 60.00 3.335 0.156 3.8 10/15/09 40,546,864.1 281.51,840.02,930.8 278 60.00 3.437 0.161 3.8 10/15/09 40,677,857.1 281.8 1,840.02,940.3 279 60.00 3.276 0.154 4.1 10/15/09 40,617,762.0 282.0 1,840.02,936.0 279 60.00 3.305 0.155 4.2 10/15/09 40,815,336.7 283.0 1,840.02,950.2 280 60.00 3.550 0.167 4.2 10/15/09 40,936,113.5 283.2 1,840.02,936.7 281 60.00 3.631 0.171 4.0 10/15/09 40,797,448.7 281.7 1,840.02,948.9 281 60.00 3.670 0.173 3.8 10/15/09 40,729,095.6 281.9 1,840.02,899.7 279 60.00 3.500 0.162 3.3 10/15/09 39,222,806.5 275.4 1,840.02,771.2 262 60.00 3.382 0.150 3.6 10/15/09 33,149,971.4 276.3 1,840.02,252.0 218 60.00 3.065 0.110 3.9 10/15/09 40,565,854.9 282.51,840.02,888.1 278 60.00 3.142 0.145 4.0 10/15/09 40,501,422.6 282.9 1,840.02,949.5 280 60.00 3.344 0.157 4.2 10/15/09 40,994,617.5 281.7 1,840.02,985.5 283 60.00 3.421 0.163 4.0 10/15/09 40,921,309.3 279.7 1,840.02,913.4 279 60.00 3.687 0.172 3.9 10/15/09 42,321,461.0 279.6 1,840.03,013.1 285 60.00 3.470 0.167 3.7 10/15/09 36,492,096.8 273.8 1,840.02,598.1 237 60.00 3.375 0.140 3.3 10/15/09 37,417,848.3 273.8 1,840.02,664.0 243 60.00 3.266 0.139 3.5 10/15/09 34,595,729.4 271.2 1,840.02,463.1 219 60.00 2.893 0.114 3.6 10/15/09 35,314,815.2 272.2 1,840.02,437.5 229 60.00 3.144 0.123 3.7 10/15/09 35,635,595.6 272.51,840.02,440.3 231 60.00 3.263 0.127 3.9 10/14/09 36,079,805.7 273.0 1,840.02,529.5 234 60.00 3.246 0.132 4.0 10/14/09 35,519,907.8 273.9 1,840.02,471.0 231 60.00 3.470 0.137 4.0 10/14/09 39,819,539.1 277.2 1,840.02,835.0 267 60.00 3.491 0.158 4.3 10/14/09 40,213,080.8 277.8 1,840.02,884.8 271 60.00 3.515 0.162 4.3 10/14/09 41,016,445.5 278.2 1,840.02,920.2 277 60.00 3.750 0.176 10/14/09 41,111,487.5 278.8 1,840.02,926.9 277 60.00 3.802 0.178

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 4.6 4.5 10/17/09 42,229,187.9 285.7 1,840.02,960.6 276 60.00 4.067 0.192 4.4 10/17/09 40,629,222.0 283.4 1,840.02,914.7 270 60.00 3.943 0.184 4.5 10/17/09 40,014,774.9 284.0 1,840.02,870.6 268 60.00 3.825 0.175 4.3 10/17/09 40,025,334.6 282.7 1,840.02,871.4 268 60.00 3.957 0.181 4.3 10/17/09 39,697,665.5 284.2 1,840.02,869.5 268 60.00 3.710 0.170 4.2 10/17/09 40,179,913.5 282.9 1,840.02,882.5 271 60.00 3.693 0.171 4.2 10/17/09 39,869,336.6 282.8 1,840.02,838.5 266 60.00 3.681 0.168 4.5 10/17/09 39,989,646.9 284.51,840.02,868.8 268 60.00 3.647 0.168 4.4 10/17/09 39,819,061.7 284.51,840.02,899.9 269 60.00 3.855 0.179 4.4 10/17/09 39,856,465.6 283.9 1,840.02,924.2 271 60.00 3.756 0.176 4.3 10/17/09 40,226,219.5 284.1 1,840.02,929.5 271 60.00 3.735 0.175 4.5 10/17/09 39,911,049.6 283.6 1,840.02,884.9 268 60.00 3.716 0.172 4.9 10/17/09 41,124,581.9 284.3 1,840.02,950.3 277 60.00 3.934 0.185 4.7 10/17/09 40,296,826.2 284.0 1,840.02,912.8 272 60.00 4.182 0.195 4.4 10/17/09 39,821,289.9 283.4 1,840.02,900.0 269 60.00 4.062 0.188 4.3 10/17/09 39,391,851.1 282.0 1,840.02,847.4 261 60.00 3.799 0.173 4.2 10/17/09 37,022,272.1 280.51,840.02,615.7 242 60.00 3.835 0.160 4.7 10/17/09 36,886,067.9 280.4 1,840.02,586.0 240 60.00 3.768 0.156 4.9 10/17/09 36,582,678.6 284.8 1,840.02,564.8 242 60.00 4.219 0.173 4.9 10/17/09 40,326,212.8 285.6 1,840.02,871.0 269 60.00 4.269 0.196 4.9 10/16/09 39,961,472.0 284.3 1,840.02,845.0 267 60.00 4.311 0.196 4.7 10/16/09 39,948,836.1 282.2 1,840.02,865.9 267 60.00 4.218 0.193 4.8 10/16/09 39,700,279.4 284.1 1,840.02,848.0 267 60.00 4.064 0.185 4.7 10/16/09 41,380,077.8 284.4 1,840.02,968.6 278 60.00 4.185 0.199 4.6 10/16/09 41,102,451.1 284.2 1,840.02,948.6 273 60.00 4.144 0.195 4.6 10/16/09 40,639,976.3 284.8 1,840.02,915.5 271 60.00 4.027 0.187 4.5 10/16/09 40,619,657.9 285.0 1,840.02,936.1 276 60.00 3.954 0.186 4.6 10/16/09 40,004,526.5 284.6 1,840.02,956.9 272 60.00 3.849 0.181 4.5 10/16/09 40,297,795.3 284.51,840.02,934.7 274 60.00 3.933 0.184 5.0 10/16/09 40,170,482.6 286.9 1,840.02,881.8 270 60.00 3.895 0.180 4.9 10/16/09 40,249,189.2 288.9 1,840.02,909.3 273 60.00 4.321 0.202 4.9 10/16/09 40,506,765.0 287.9 1,840.02,950.0 276 60.00 4.227 0.199 4.9 10/16/09 40,692,312.6 287.1 1,840.02,941.3 276 60.00 4.268 0.201 4.8 10/16/09 40,217,883.2 286.4 1,840.02,928.9 272 60.00 4.185 0.196 4.6 10/16/09 40,632,394.0 286.0 1,840.02,959.1 277 60.00 4.109 0.195 4.6 10/16/09 40,451,765.8 284.2 1,840.02,967.9 277 60.00 3.932 0.186 10/16/09 40,946,358.2 284.1 1,840.02,981.9 279 60.00 3.984 0.189

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 3.7 3.7 10/19/09 40,879,915.1 283.51,840.02,954.9 279 60.00 3.197 0.151 4.2 10/19/09 40,794,893.5 282.9 1,840.02,948.8 277 60.00 3.210 0.151 4.2 10/19/09 40,118,159.4 282.2 1,840.02,878.0 269 60.00 3.640 0.167 3.0 10/19/09 39,258,454.5 277.7 1,840.02,816.3 263 60.00 3.604 0.163 3.6 10/19/09 33,562,166.0 272.4 1,840.02,334.7 213 60.00 2.731 0.102 3.2 10/19/09 31,577,969.2 272.4 1,840.02,196.7 201 60.00 3.251 0.114 3.4 10/19/09 28,193,763.0 265.0 1,840.0 1,900.0 176 60.00 2.971 0.090 2.9 10/19/09 27,972,429.1 253.9 1,840.0 1,900.3 179 60.00 3.089 0.094 2.9 10/19/09 28,761,156.4 246.4 1,840.0 1,969.5 182 60.00 2.688 0.085 3.0 10/18/09 25,031,232.3 249.6 1,840.0 1,700.5 158 60.00 2.636 0.071 4.0 10/18/09 27,408,974.6 262.9 1,840.0 1,862.0 180 60.00 2.789 0.083 4.2 10/18/09 36,782,619.0 279.7 1,840.02,618.8 247 60.00 3.522 0.147 4.2 10/18/09 40,033,819.5 284.6 1,840.02,893.8 271 60.00 3.594 0.167 4.1 10/18/09 40,437,665.9 285.2 1,840.02,944.9 275 60.00 3.617 0.170 4.5 10/18/09 39,739,753.8 285.51,840.02,872.5 270 60.00 3.522 0.162 4.5 10/18/09 40,567,021.6 286.8 1,840.02,888.2 273 60.00 3.981 0.184 4.4 10/18/09 41,221,326.2 286.4 1,840.02,845.1 270 60.00 4.040 0.184 4.2 10/18/09 41,188,359.5 283.9 1,840.02,842.9 269 60.00 3.951 0.180 4.1 10/18/09 40,370,271.3 285.3 1,840.02,786.4 261 60.00 3.804 0.169 4.1 10/18/09 39,583,033.8 281.4 1,840.02,732.1 254 60.00 3.693 0.161 4.2 10/18/09 39,615,111.5 284.9 1,840.02,712.8 255 60.00 3.764 0.163 4.4 10/18/09 42,051,184.5 286.1 1,840.02,902.4 273 60.00 3.809 0.177 4.6 10/18/09 41,415,026.6 286.8 1,840.02,858.5 270 60.00 3.986 0.183 4.4 10/18/09 42,062,518.1 286.7 1,840.02,949.0 276 60.00 4.102 0.193 4.2 10/18/09 41,217,179.2 283.8 1,840.02,867.3 268 60.00 3.914 0.180 4.3 10/18/09 39,570,454.4 281.51,840.02,731.2 251 60.00 3.786 0.165 4.4 10/18/09 39,824,283.6 282.6 1,840.02,748.7 255 60.00 3.933 0.173 3.9 10/18/09 37,586,029.1 276.8 1,840.02,594.3 235 60.00 3.991 0.165 4.0 10/18/09 30,761,103.3 270.8 1,840.02,123.2 192 60.00 3.562 0.121 4.0 10/18/09 29,631,195.4 272.6 1,840.0 1,980.8 188 60.00 3.735 0.119 3.9 10/18/09 31,992,092.3 273.0 1,840.02,208.1 208 60.00 3.644 0.128 3.9 10/18/09 29,684,497.7 270.7 1,840.0 1,952.0 184 60.00 3.732 0.116 3.8 10/18/09 29,712,001.0 271.51,840.0 1,986.2 182 60.00 3.676 0.117 4.2 10/17/09 30,238,551.0 273.51,840.02,037.8 188 60.00 3.565 0.116 4.6 10/17/09 31,454,566.0 277.51,840.02,154.0 203 60.00 3.826 0.131 4.4 10/17/09 39,862,085.2 284.9 1,840.02,773.0 258 60.00 4.140 0.183 10/17/09 40,837,204.5 285.1 1,840.02,863.0 266 60.00 3.964 0.181

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 4.1 4.2 10/20/09 40,695,263.9 281.0 1,840.02,941.5 275 60.00 3.548 0.167 4.2 10/20/09 41,227,797.1 281.2 1,840.02,957.7 278 60.00 3.607 0.171 4.3 10/20/09 41,501,774.2 281.2 1,840.02,977.3 281 60.00 3.628 0.173 4.4 10/20/09 41,383,533.1 280.6 1,840.02,968.9 280 60.00 3.761 0.179 4.2 10/20/09 41,754,498.6 280.3 1,840.02,995.4 282 60.00 3.809 0.182 4.4 10/20/09 40,831,926.0 278.51,840.02,884.9 274 60.00 3.735 0.173 4.4 10/20/09 41,671,751.6 279.1 1,840.02,921.6 277 60.00 3.910 0.183 4.6 10/20/09 41,405,318.6 279.1 1,840.02,902.9 275 60.00 3.938 0.182 4.7 10/20/09 40,923,407.9 280.8 1,840.02,869.1 272 60.00 4.123 0.189 5.1 10/20/09 41,092,462.6 285.6 1,840.02,925.6 275 60.00 4.117 0.193 5.0 10/20/09 41,869,930.2 284.51,840.02,981.0 280 60.00 4.500 0.215 5.1 10/20/09 41,572,853.9 279.8 1,840.02,937.2 276 60.00 4.423 0.208 5.2 10/20/09 41,223,892.7 280.1 1,840.02,912.6 274 60.00 4.503 0.209 5.1 10/20/09 42,261,396.5 279.0 1,840.02,985.8 281 60.00 4.598 0.219 5.4 10/20/09 42,323,072.1 278.0 1,840.02,990.2 281 60.00 4.463 0.214 5.6 10/20/09 41,492,054.5 280.0 1,840.02,841.3 273 60.00 4.870 0.222 4.9 10/20/09 41,885,697.6 277.8 1,840.02,913.8 275 60.00 4.997 0.233 4.7 10/20/09 34,572,330.6 271.8 1,840.02,386.2 219 60.00 4.406 0.168 4.1 10/20/09 32,853,389.4 270.9 1,840.02,321.1 211 60.00 4.143 0.153 4.1 10/20/09 29,475,832.4 269.0 1,840.02,098.6 185 60.00 3.572 0.120 4.1 10/20/09 28,143,323.2 270.4 1,840.0 1,927.2 172 60.00 3.720 0.115 3.5 10/20/09 30,423,885.9 267.8 1,840.02,099.9 190 60.00 3.693 0.124 3.7 10/19/09 29,194,393.6 259.8 1,840.02,078.5 189 60.00 3.070 0.102 4.3 10/19/09 33,559,309.2 268.4 1,840.02,316.3 219 60.00 3.318 0.123 4.5 10/19/09 37,874,349.8 276.4 1,840.02,717.0 253 60.00 3.753 0.163 4.6 10/19/09 40,451,608.9 282.7 1,840.02,902.0 274 60.00 3.916 0.182 4.6 10/19/09 41,382,687.9 283.7 1,840.02,991.3 282 60.00 3.955 0.189 4.5 10/19/09 40,691,305.0 283.1 1,840.02,941.3 278 60.00 3.997 0.188 4.5 10/19/09 40,724,376.0 283.0 1,840.02,965.8 278 60.00 3.876 0.184 4.6 10/19/09 40,058,824.7 285.0 1,840.02,895.6 270 60.00 3.926 0.182 4.4 10/19/09 40,829,258.3 284.51,840.02,929.0 275 60.00 3.957 0.186 4.4 10/19/09 40,711,452.5 282.8 1,840.02,920.6 274 60.00 3.793 0.177 4.3 10/19/09 39,592,520.4 284.0 1,840.02,840.4 267 60.00 3.825 0.174 3.9 10/19/09 40,622,864.5 285.1 1,840.02,936.3 275 60.00 3.739 0.176 3.6 10/19/09 40,882,408.5 282.1 1,840.02,932.8 278 60.00 3.423 0.161 3.8 10/19/09 40,658,749.7 282.6 1,840.02,938.9 279 60.00 3.108 0.146 10/19/09 40,654,473.4 282.51,840.02,938.6 278 60.00 3.236 0.152

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 4.5 4.6 10/22/09 40,634,237.6 278.7 1,840.02,848.8 271 60.00 4.048 0.184 4.8 10/22/09 40,375,952.5 278.9 1,840.02,808.8 270 60.00 4.081 0.184 4.6 10/22/09 41,063,486.2 279.7 1,840.02,878.9 276 60.00 4.253 0.196 3.9 10/22/09 41,208,375.9 280.2 1,840.02,911.4 276 60.00 4.071 0.189 3.7 10/22/09 39,866,297.7 277.8 1,840.02,816.6 267 60.00 3.450 0.156 4.0 10/22/09 35,656,594.9 273.4 1,840.02,519.2 232 60.00 3.256 0.131 3.8 10/22/09 33,656,117.7 273.3 1,840.02,286.4 218 60.00 3.632 0.133 3.8 10/22/09 35,954,491.2 274.4 1,840.02,462.1 233 60.00 3.434 0.135 3.5 10/22/09 36,988,769.8 273.51,840.02,512.8 237 60.00 3.507 0.141 3.5 10/22/09 33,033,972.7 270.8 1,840.02,316.0 210 60.00 3.135 0.116 3.2 10/22/09 33,508,287.9 272.2 1,840.02,276.4 215 60.00 3.248 0.118 3.4 10/21/09 33,104,729.4 272.4 1,840.02,338.9 220 60.00 2.840 0.106 4.0 10/21/09 37,652,637.7 278.1 1,840.02,660.3 253 60.00 3.025 0.129 4.2 10/21/09 41,093,089.1 280.2 1,840.02,948.0 279 60.00 3.476 0.164 4.2 10/21/09 40,991,675.6 280.51,840.02,918.5 276 60.00 3.690 0.172 4.1 10/21/09 40,793,596.0 281.3 1,840.02,926.5 277 60.00 3.662 0.171 4.1 10/21/09 40,730,731.0 281.0 1,840.02,944.1 279 60.00 3.576 0.168 4.4 10/21/09 40,466,465.8 280.6 1,840.02,925.0 274 60.00 3.555 0.166 4.4 10/21/09 40,818,269.8 279.6 1,840.02,861.7 273 60.00 3.882 0.178 4.3 10/21/09 41,260,821.8 279.51,840.02,892.8 277 60.00 3.954 0.183 4.3 10/21/09 41,022,822.6 279.3 1,840.02,831.5 271 60.00 3.859 0.175 4.5 10/21/09 40,847,832.3 279.51,840.02,819.4 273 60.00 3.863 0.175 4.4 10/21/09 41,542,394.0 279.8 1,840.02,957.6 278 60.00 3.904 0.185 4.0 10/21/09 41,302,860.7 279.4 1,840.02,940.6 275 60.00 3.819 0.180 4.3 10/21/09 37,739,202.0 274.7 1,840.02,707.4 248 60.00 3.481 0.150 4.3 10/21/09 38,701,644.9 278.51,840.02,797.5 258 60.00 3.661 0.164 4.3 10/21/09 41,527,295.5 280.0 1,840.02,956.5 280 60.00 3.768 0.179 3.9 10/21/09 41,993,008.1 281.2 1,840.02,989.7 282 60.00 3.748 0.179 3.8 10/21/09 41,856,108.5 280.9 1,840.03,025.5 281 60.00 3.375 0.164 4.0 10/21/09 39,283,623.6 277.51,840.02,775.5 258 60.00 3.358 0.149 3.9 10/21/09 40,111,352.2 279.0 1,840.02,833.9 265 60.00 3.529 0.160 4.0 10/21/09 39,273,907.6 277.9 1,840.02,753.4 259 60.00 3.484 0.153 3.8 10/21/09 39,847,107.0 279.4 1,840.02,836.9 268 60.00 3.500 0.159 3.9 10/21/09 40,907,674.4 279.0 1,840.02,956.9 277 60.00 3.291 0.156 4.0 10/21/09 41,088,789.0 279.8 1,840.02,947.7 275 60.00 3.419 0.161 3.9 10/20/09 40,838,658.8 280.1 1,840.02,907.6 273 60.00 3.495 0.163 10/20/09 41,037,331.0 281.0 1,840.02,944.0 275 60.00 3.382 0.159

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 * * 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 2.8 3.1 10/23/09 36,850,328.5 275.8 1,840.02,563.5 243 60.00 2.497 0.102 3.4 10/23/09 36,653,758.9 272.9 1,840.02,589.7 238 60.00 2.736 0.113 3.3 10/23/09 36,901,629.1 274.4 1,840.02,607.2 245 60.00 3.054 0.127 3.3 10/23/09 39,606,590.6 277.8 1,840.02,841.4 266 60.00 2.888 0.131 3.4 10/23/09 40,211,158.1 278.7 1,840.02,906.6 273 60.00 2.891 0.134 3.6 10/23/09 40,922,343.3 279.2 1,840.02,935.7 276 60.00 2.954 0.139 3.3 10/23/09 40,211,686.6 275.8 1,840.02,841.1 267 60.00 3.136 0.143 3.1 10/23/09 38,764,037.4 275.0 1,840.02,675.6 256 60.00 2.929 0.126 3.3 10/23/09 40,376,227.3 276.51,840.02,830.7 269 60.00 2.800 0.127 3.3 10/23/09 40,083,536.2 276.3 1,840.02,766.7 268 60.00 2.988 0.132 3.3 10/23/09 40,420,983.6 276.1 1,840.02,789.9 269 60.00 2.996 0.133 3.3 10/23/09 40,025,940.9 276.0 1,840.02,719.2 268 60.00 2.999 0.131 3.1 10/23/09 39,876,115.2 275.8 1,840.02,860.7 270 60.00 2.893 0.132 3.3 10/23/09 39,849,573.4 275.3 1,840.02,837.1 270 60.00 2.697 0.122 3.4 10/23/09 40,304,711.8 275.4 1,840.02,803.8 270 60.00 2.933 0.132 3.7 10/23/09 40,282,090.4 275.7 1,840.02,824.1 271 60.00 3.027 0.137 3.9 10/23/09 39,995,431.0 276.2 1,840.02,847.5 271 60.00 3.216 0.147 3.9 10/23/09 39,534,266.1 275.8 1,840.02,836.1 269 60.00 3.382 0.154 3.3 10/23/09 38,390,154.9 272.4 1,840.02,712.3 255 60.00 3.457 0.150 3.4 10/23/09 33,373,114.8 267.51,840.02,267.2 216 60.00 3.053 0.111 2.9 10/23/09 31,796,879.0 266.2 1,840.02,142.8 206 60.00 3.123 0.107 2.8 10/23/09 28,849,138.7 262.6 1,840.0 1,959.9 181 60.00 2.682 0.084 2.9 10/23/09 26,066,251.1 264.2 1,840.0 1,700.0 163 60.00 2.723 0.074 3.2 10/23/09 27,884,820.4 265.51,840.0 1,833.7 174 60.00 2.705 0.079 3.2 10/22/09 30,455,429.7 269.51,840.02,052.4 195 60.00 2.981 0.098 3.4 10/22/09 34,006,629.7 274.2 1,840.02,384.2 223 60.00 2.861 0.109 3.7 10/22/09 36,113,039.0 274.9 1,840.02,649.6 240 60.00 2.864 0.121 3.9 10/22/09 36,854,077.4 276.1 1,840.02,583.8 244 60.00 3.258 0.135 4.1 10/22/09 38,798,410.5 277.9 1,840.02,783.3 260 60.00 3.418 0.152 3.9 10/22/09 39,475,168.5 278.1 1,840.02,874.8 267 60.00 3.513 0.161 3.8 10/22/09 39,897,855.9 277.9 1,840.02,883.9 270 60.00 3.368 0.155 3.7 10/22/09 39,938,183.1 277.6 1,840.02,865.1 270 60.00 3.265 0.150 3.7 10/22/09 39,523,039.3 276.1 1,840.02,813.9 266 60.00 3.190 0.144 3.9 10/22/09 38,817,590.2 276.51,840.02,784.8 261 60.00 3.187 0.142 4.4 10/22/09 39,632,568.8 278.0 1,840.02,800.2 267 60.00 3.389 0.152 4.5 10/22/09 40,008,438.7 278.6 1,840.02,848.4 268 60.00 3.823 0.174 10/22/09 40,675,387.1 279.1 1,840.02,873.8 271 60.00 4.005 0.184

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 4.6 4.4 10/25/09 38,422,761.3 276.1 1,840.02,756.4 255 60.00 4.037 0.177 4.3 10/25/09 37,644,580.6 275.0 1,840.02,700.6 250 60.00 3.845 0.166 4.1 10/25/09 36,887,017.4 273.8 1,840.02,646.2 241 60.00 3.740 0.158 3.6 10/25/09 35,957,442.9 274.7 1,840.02,560.0 235 60.00 3.625 0.148 3.6 10/25/09 34,533,503.9 271.2 1,840.02,439.9 219 60.00 3.202 0.125 3.5 10/25/09 32,760,598.7 269.8 1,840.02,279.0 209 60.00 3.182 0.116 2.8 10/25/09 34,091,847.2 270.3 1,840.02,408.7 220 60.00 3.123 0.120 3.0 10/25/09 32,984,275.5 269.8 1,840.02,312.5 210 60.00 2.536 0.094 2.4 10/25/09 32,330,571.3 268.4 1,840.02,249.1 205 60.00 2.699 0.097 2.8 10/25/09 29,828,688.4 268.3 1,840.02,042.6 186 60.00 2.206 0.072 2.9 10/25/09 31,920,887.2 269.2 1,840.02,220.6 209 60.00 2.494 0.088 3.3 10/25/09 28,974,865.3 268.2 1,840.02,031.4 183 60.00 2.576 0.084 3.0 10/25/09 31,130,277.1 271.8 1,840.02,199.4 202 60.00 2.886 0.102 2.8 10/24/09 35,717,448.6 271.1 1,840.02,523.5 228 60.00 2.645 0.107 3.0 10/24/09 31,382,841.7 271.3 1,840.02,200.2 202 60.00 2.537 0.089 3.3 10/24/09 35,991,861.3 276.0 1,840.02,582.0 239 60.00 2.617 0.108 3.7 10/24/09 40,361,839.8 279.8 1,840.02,939.4 271 60.00 2.818 0.132 4.0 10/24/09 40,803,515.1 279.3 1,840.02,993.8 276 60.00 3.165 0.151 3.6 10/24/09 39,001,879.6 277.8 1,840.02,840.4 263 60.00 3.414 0.154 3.7 10/24/09 39,399,898.9 278.8 1,840.02,890.8 267 60.00 3.084 0.142 4.0 10/24/09 39,541,544.8 279.0 1,840.02,879.7 268 60.00 3.143 0.145 3.8 10/24/09 39,530,442.0 278.6 1,840.02,878.8 269 60.00 3.418 0.158 3.7 10/24/09 38,772,116.2 277.51,840.02,823.6 263 60.00 3.230 0.146 3.9 10/24/09 39,561,050.8 278.51,840.02,881.1 268 60.00 3.135 0.145 4.0 10/24/09 39,909,345.4 279.0 1,840.02,884.7 270 60.00 3.342 0.155 4.3 10/24/09 40,392,384.3 278.7 1,840.02,897.7 271 60.00 3.471 0.161 4.5 10/24/09 40,104,758.0 279.4 1,840.02,877.1 270 60.00 3.786 0.174 4.2 10/24/09 39,663,537.2 278.4 1,840.02,845.5 269 60.00 3.893 0.178 4.2 10/24/09 39,431,843.7 277.9 1,840.02,828.8 267 60.00 3.639 0.165 4.1 10/24/09 39,632,005.5 277.1 1,840.02,843.2 266 60.00 3.658 0.166 3.9 10/24/09 38,689,413.6 276.51,840.02,628.3 253 60.00 3.768 0.158 4.2 10/24/09 38,719,989.0 275.6 1,840.02,714.6 255 60.00 3.474 0.151 3.8 10/24/09 39,271,164.9 276.3 1,840.02,731.9 261 60.00 3.775 0.164 3.8 10/24/09 38,073,600.6 274.6 1,840.02,648.6 250 60.00 3.383 0.143 3.3 10/24/09 38,500,845.5 275.9 1,840.02,657.4 254 60.00 3.403 0.144 3.3 10/24/09 37,467,567.6 273.51,840.02,606.5 244 60.00 2.936 0.122 10/24/09 35,207,496.0 271.51,840.02,410.9 227 60.00 2.978 0.115

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 6.6 6.4 10/27/09 30,175,586.4 272.0 1,840.02,099.2 191 60.00 5.879 0.197 6.6 10/27/09 30,226,968.1 272.6 1,840.02,086.3 191 60.00 5.805 0.194 6.8 10/26/09 31,042,733.1 272.7 1,840.02,159.5 199 60.00 5.922 0.205 8.3 10/26/09 30,461,814.7 273.4 1,840.02,119.1 197 60.00 6.135 0.208 9.0 10/26/09 36,870,496.3 280.1 1,840.02,604.9 245 60.00 7.369 0.306 7.0 10/26/09 39,897,470.1 282.1 1,840.02,862.2 268 60.00 7.880 0.360 5.5 10/26/09 40,824,871.7 283.9 1,840.02,928.8 277 60.00 6.049 0.284 5.4 10/26/09 41,440,273.3 285.8 1,840.02,972.9 279 60.00 4.822 0.229 5.6 10/26/09 42,396,041.6 286.3 1,840.02,972.3 279 60.00 4.765 0.226 5.8 10/26/09 41,731,855.5 283.8 1,840.02,903.1 276 60.00 5.048 0.235 5.7 10/26/09 41,593,598.8 282.9 1,840.02,916.1 277 60.00 5.183 0.241 5.0 10/26/09 41,776,450.4 283.2 1,840.02,906.2 276 60.00 5.130 0.238 4.9 10/26/09 42,157,686.6 283.51,840.02,932.7 278 60.00 4.525 0.212 4.9 10/26/09 42,429,818.2 283.51,840.02,951.7 278 60.00 4.432 0.209 4.8 10/26/09 42,200,475.9 282.9 1,840.02,958.6 278 60.00 4.397 0.208 5.0 10/26/09 42,347,454.3 283.1 1,840.02,968.9 279 60.00 4.274 0.203 5.0 10/26/09 42,337,621.0 282.4 1,840.02,968.3 278 60.00 4.504 0.213 5.0 10/26/09 42,248,899.7 282.0 1,840.02,962.0 278 60.00 4.414 0.209 5.1 10/26/09 41,543,411.6 282.2 1,840.02,889.9 270 60.00 4.489 0.208 5.3 10/26/09 42,293,673.4 282.1 1,840.02,965.2 278 60.00 4.511 0.215 4.7 10/26/09 41,075,415.6 280.3 1,840.02,835.1 267 60.00 4.791 0.216 4.9 10/26/09 40,234,908.6 277.6 1,840.02,799.0 260 60.00 4.244 0.190 4.8 10/26/09 36,784,801.1 275.0 1,840.02,479.0 234 60.00 4.480 0.178 4.6 10/26/09 35,172,053.6 272.6 1,840.02,351.2 218 60.00 4.465 0.169 4.6 10/26/09 33,314,846.1 272.0 1,840.02,299.5 210 60.00 4.108 0.152 4.3 10/26/09 31,600,320.2 270.7 1,840.02,181.1 196 60.00 4.123 0.144 3.8 10/25/09 31,546,087.6 271.1 1,840.02,194.5 198 60.00 3.867 0.136 4.3 10/25/09 31,997,975.9 273.3 1,840.02,278.1 207 60.00 3.312 0.120 4.3 10/25/09 38,376,346.3 278.9 1,840.02,753.1 253 60.00 3.775 0.166 4.6 10/25/09 38,816,448.0 278.2 1,840.02,784.6 255 60.00 3.726 0.166 4.5 10/25/09 40,128,461.3 279.4 1,840.02,878.7 264 60.00 4.009 0.184 4.5 10/25/09 40,393,433.9 279.9 1,840.02,919.7 267 60.00 3.886 0.181 4.5 10/25/09 40,429,104.4 279.4 1,840.02,856.4 265 60.00 3.979 0.182 4.3 10/25/09 40,260,199.2 279.1 1,840.02,866.3 265 60.00 3.892 0.179 4.5 10/25/09 39,215,494.5 278.1 1,840.02,791.9 257 60.00 3.766 0.169 4.5 10/25/09 37,906,252.8 275.9 1,840.02,698.7 247 60.00 3.939 0.170 10/25/09 36,493,491.9 274.9 1,840.02,578.3 238 60.00 3.957 0.163

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 MC M 11:00 C 12:00 M M 13:00 14:00 4.9 5.3 10/28/09 39,334,242.8 277.0 1,840.02,821.8 269 60.00 4.285 0.193 5.2 10/28/09 39,185,469.3 278.4 1,840.02,832.4 270 60.00 4.555 0.206 5.2 10/28/09 40,125,278.5 279.0 1,840.02,922.1 278 60.00 4.446 0.208 5.3 10/28/09 40,142,671.8 278.1 1,840.02,923.5 278 60.00 4.490 0.209 5.5 10/28/09 40,483,132.9 278.8 1,840.02,904.2 278 60.00 4.568 0.213 5.6 10/28/09 41,079,249.1 279.7 1,840.02,924.6 279 60.00 4.774 0.223 5.8 10/28/09 41,085,626.2 279.9 1,840.02,969.8 278 60.00 4.817 0.228 6.5 10/28/09 41,069,463.6 279.9 1,840.02,968.6 278 60.00 5.021 0.238 6.7 10/28/09 41,428,207.1 280.9 1,840.02,972.0 278 60.00 5.637 0.268 5.0 10/28/09 40,322,712.6 276.8 1,840.02,914.7 271 60.00 5.803 0.271 5.7 10/28/09 34,802,346.1 272.6 1,840.02,458.8 227 60.00 4.387 0.173 5.3 10/28/09 35,519,587.3 272.9 1,840.02,490.3 231 60.00 5.122 0.204 5.4 10/28/09 33,328,813.5 271.3 1,840.02,246.1 211 60.00 4.937 0.177 5.4 10/28/09 34,396,687.4 272.51,840.02,411.5 225 60.00 4.779 0.184 5.4 10/28/09 34,113,349.0 273.2 1,840.02,391.6 226 60.00 4.774 0.183 5.6 10/27/09 35,846,861.8 272.51,840.02,552.2 236 60.00 4.745 0.194 6.2 10/27/09 33,559,093.4 273.2 1,840.02,352.8 220 60.00 4.994 0.188 5.7 10/27/09 38,029,809.6 276.2 1,840.02,666.2 253 60.00 5.505 0.235 6.3 10/27/09 38,806,430.9 278.2 1,840.02,720.6 258 60.00 5.072 0.221 6.5 10/27/09 39,214,834.4 279.51,840.02,770.6 265 60.00 5.554 0.246 6.8 10/27/09 39,206,430.3 280.1 1,840.02,855.2 267 60.00 5.575 0.254 6.5 10/27/09 39,902,334.9 280.2 1,840.02,884.2 273 60.00 5.854 0.270 6.4 10/27/09 40,594,201.5 280.51,840.02,912.2 275 60.00 5.680 0.264 6.4 10/27/09 40,567,460.6 281.0 1,840.02,910.2 275 60.00 5.552 0.258 6.7 10/27/09 40,361,389.7 281.1 1,840.02,873.5 273 60.00 5.606 0.258 7.6 10/27/09 39,919,911.7 282.6 1,840.02,842.1 268 60.00 5.922 0.268 7.8 10/27/09 40,226,113.3 283.4 1,840.02,863.9 272 60.00 6.662 0.306 7.8 10/27/09 40,328,799.4 283.8 1,840.02,871.2 272 60.00 6.840 0.313 7.7 10/27/09 40,134,534.7 283.7 1,840.02,922.9 273 60.00 6.730 0.314 7.5 10/27/09 39,917,194.9 282.8 1,840.02,907.0 272 60.00 6.628 0.308 7.6 10/27/09 40,487,725.8 281.1 1,840.02,948.6 277 60.00 6.414 0.303 7.3 10/27/09 40,202,000.1 280.1 1,840.02,905.9 273 60.00 6.558 0.305 5.7 10/27/09 39,659,095.0 277.9 1,840.02,823.5 263 60.00 6.433 0.291 5.6 10/27/09 30,405,455.6 266.8 1,840.02,115.1 185 60.00 5.130 0.173 6.5 10/27/09 27,957,475.1 270.1 1,840.0 1,823.3 173 60.00 5.336 0.155 6.3 10/27/09 31,923,313.9 274.1 1,840.02,186.0 204 60.00 5.906 0.207 10/27/09 30,129,510.7 271.8 1,840.02,079.6 192 60.00 5.668 0.188

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 C 10:00 C 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 3.0 3.0 10/30/09 26,832,333.5 263.51,840.0 1,808.2 173 60.00 2.746 0.080 3.1 10/30/09 25,930,288.6 264.0 1,840.0 1,761.5 169 60.00 2.766 0.078 3.1 10/30/09 24,999,883.6 264.2 1,840.0 1,698.4 158 60.00 2.798 0.076 3.1 10/30/09 28,327,731.8 267.7 1,840.0 1,909.1 183 60.00 2.824 0.086 3.2 10/29/09 31,010,968.5 269.0 1,840.02,123.6 202 60.00 2.816 0.096 3.2 10/29/09 31,108,983.8 269.51,840.02,164.1 209 60.00 2.853 0.099 3.7 10/29/09 32,567,881.3 271.0 1,840.02,265.6 218 60.00 2.915 0.105 4.5 10/29/09 37,587,738.4 275.7 1,840.02,655.7 257 60.00 3.283 0.139 5.7 10/29/09 39,835,492.2 277.3 1,840.02,836.1 272 60.00 3.930 0.178 5.7 10/29/09 39,987,665.8 277.1 1,840.02,847.0 273 60.00 5.046 0.229 5.4 10/29/09 40,297,814.1 277.2 1,840.02,825.2 272 60.00 5.056 0.229 5.1 10/29/09 39,960,820.7 276.6 1,840.02,845.0 272 60.00 4.725 0.215 5.3 10/29/09 40,327,972.8 276.3 1,840.02,871.2 274 60.00 4.449 0.205 5.4 10/29/09 40,536,961.7 277.51,840.02,886.1 274 60.00 4.620 0.214 5.4 10/29/09 40,649,495.4 277.8 1,840.02,916.1 275 60.00 4.674 0.217 5.6 10/29/09 40,639,229.5 278.3 1,840.02,893.3 275 60.00 4.737 0.219 5.5 10/29/09 40,493,981.1 277.2 1,840.02,949.0 277 60.00 4.793 0.226 5.4 10/29/09 40,507,497.9 277.3 1,840.02,950.0 277 60.00 4.675 0.221 5.5 10/29/09 40,103,100.5 277.3 1,840.02,920.5 272 60.00 4.673 0.218 5.3 10/29/09 40,211,499.2 277.3 1,840.02,950.3 274 60.00 4.666 0.220 5.3 10/29/09 40,211,617.6 276.9 1,840.02,862.9 273 60.00 4.666 0.214 5.2 10/29/09 40,570,855.4 277.51,840.02,932.6 276 60.00 4.590 0.215 4.1 10/29/09 40,349,087.5 276.7 1,840.02,916.5 273 60.00 4.479 0.209 4.2 10/29/09 38,005,270.8 272.9 1,840.02,726.4 249 60.00 3.530 0.154 3.9 10/29/09 31,729,572.4 268.7 1,840.02,224.5 212 60.00 3.756 0.134 3.5 10/29/09 29,962,453.3 266.8 1,840.02,100.6 202 60.00 3.483 0.117 3.6 10/29/09 28,752,761.1 267.3 1,840.02,015.8 189 60.00 3.141 0.101 3.5 10/29/09 30,729,240.7 268.7 1,840.02,154.4 204 60.00 3.172 0.109 3.8 10/28/09 31,190,282.4 269.3 1,840.02,186.7 205 60.00 3.107 0.109 4.4 10/28/09 33,280,687.4 271.8 1,840.02,369.5 223 60.00 3.320 0.126 4.4 10/28/09 39,050,099.4 276.2 1,840.02,801.4 266 60.00 3.811 0.171 4.4 10/28/09 39,791,290.3 276.3 1,840.02,854.6 272 60.00 3.820 0.174 4.6 10/28/09 39,668,203.4 276.8 1,840.02,845.7 270 60.00 3.861 0.176 4.9 10/28/09 39,907,155.2 277.7 1,840.02,884.6 274 60.00 4.005 0.185 4.9 10/28/09 40,399,739.1 277.9 1,840.02,942.2 278 60.00 4.237 0.199 4.9 10/28/09 39,258,943.0 275.4 1,840.02,837.7 272 60.00 4.260 0.193 10/28/09 39,095,597.1 276.6 1,840.02,804.7 270 60.00 4.293 0.192

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 6.3 6.3 10/31/09 39,974,693.1 277.7 1,840.02,846.0 271 60.00 5.538 0.251 6.0 10/31/09 38,867,585.6 276.8 1,840.02,725.0 260 60.00 5.580 0.243 5.6 10/31/09 38,582,157.5 276.3 1,840.02,684.0 257 60.00 5.336 0.230 5.2 10/31/09 37,638,357.1 277.4 1,840.02,618.3 252 60.00 4.993 0.210 4.6 10/31/09 38,177,524.6 276.8 1,840.02,718.1 258 60.00 4.598 0.199 4.8 10/31/09 38,583,283.8 277.1 1,840.02,726.0 262 60.00 4.047 0.177 5.0 10/31/09 38,953,814.4 277.2 1,840.02,773.4 261 60.00 4.218 0.187 5.0 10/31/09 39,606,577.9 277.2 1,840.02,755.3 262 60.00 4.504 0.198 4.6 10/31/09 39,609,833.7 276.7 1,840.02,755.5 264 60.00 4.504 0.198 3.8 10/31/09 40,800,120.7 276.51,840.02,860.4 275 60.00 4.093 0.187 2.9 10/31/09 39,124,567.2 273.3 1,840.02,785.5 264 60.00 3.364 0.150 2.6 10/31/09 31,764,061.8 265.3 1,840.02,244.2 208 60.00 2.535 0.091 2.5 10/31/09 27,393,309.4 264.7 1,840.0 1,875.8 177 60.00 2.356 0.071 2.4 10/31/09 28,415,723.8 265.0 1,840.0 1,930.4 183 60.00 2.340 0.072 2.7 10/31/09 26,549,164.5 264.0 1,840.0 1,760.3 168 60.00 2.219 0.062 2.8 10/31/09 26,313,299.9 263.1 1,840.0 1,816.2 171 60.00 2.394 0.070 3.1 10/31/09 25,552,013.8 265.51,840.0 1,763.6 169 60.00 2.568 0.073 2.8 10/30/09 30,743,331.0 268.1 1,840.02,138.6 203 60.00 2.760 0.094 2.7 10/30/09 30,281,494.6 269.0 1,840.02,123.0 202 60.00 2.524 0.086 3.4 10/30/09 31,720,367.4 269.1 1,840.02,241.1 208 60.00 2.416 0.087 3.6 10/30/09 33,760,240.0 272.4 1,840.02,348.5 229 60.00 3.080 0.116 3.5 10/30/09 37,152,670.3 273.6 1,840.02,624.9 253 60.00 3.198 0.135 2.8 10/30/09 39,009,576.5 274.7 1,840.02,756.1 268 60.00 3.069 0.135 2.5 10/30/09 39,975,392.9 274.4 1,840.02,824.3 272 60.00 2.507 0.113 2.9 10/30/09 36,599,054.1 273.7 1,840.02,565.9 246 60.00 2.186 0.090 3.5 10/30/09 38,842,985.5 274.0 1,840.02,744.3 261 60.00 2.585 0.113 3.8 10/30/09 37,309,024.7 274.2 1,840.02,615.7 252 60.00 3.104 0.130 3.5 10/30/09 39,779,299.7 276.1 1,840.02,810.5 271 60.00 3.351 0.151 3.2 10/30/09 39,638,305.5 276.4 1,840.02,822.1 270 60.00 3.064 0.138 3.5 10/30/09 40,573,285.8 277.4 1,840.02,888.6 277 60.00 2.849 0.131 4.1 10/30/09 39,026,209.9 279.6 1,840.02,820.9 271 60.00 3.008 0.135 3.7 10/30/09 39,578,427.0 284.2 1,840.02,817.8 272 60.00 3.546 0.160 3.2 10/30/09 40,115,042.5 276.1 1,840.02,856.0 274 60.00 3.258 0.149 3.5 10/30/09 38,956,904.1 275.3 1,840.02,752.4 265 60.00 2.785 0.123 3.6 10/30/09 38,664,319.9 275.1 1,840.02,731.7 262 60.00 3.081 0.134 2.4 10/30/09 37,743,051.6 271.2 1,840.02,666.6 252 60.00 3.212 0.137 10/30/09 30,569,284.8 264.1 1,840.02,093.3 196 60.00 2.222 0.074

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 3.4 3.7 11/02/09 28,224,639.3 266.4 1,840.02,009.5 183 60.00 2.962 0.095 3.7 11/02/09 26,541,161.9 266.3 1,840.0 1,788.6 164 60.00 3.416 0.098 3.5 11/02/09 25,240,602.3 264.6 1,840.0 1,673.6 153 60.00 3.506 0.094 4.1 11/02/09 25,188,283.2 265.3 1,840.0 1,574.3 154 60.00 3.525 0.089 2.7 11/02/09 27,266,147.0 264.7 1,840.0 1,852.3 167 60.00 3.792 0.112 2.9 11/02/09 23,995,771.3 265.3 1,840.0 1,604.1 150 60.00 2.477 0.064 3.3 11/01/09 26,865,978.3 268.51,840.0 1,898.1 174 60.00 2.566 0.078 3.6 11/01/09 28,855,286.9 269.51,840.02,054.4 186 60.00 2.920 0.096 4.7 11/01/09 28,383,597.4 273.1 1,840.02,020.8 192 60.00 3.143 0.102 4.8 11/01/09 37,569,834.7 278.3 1,840.02,674.8 256 60.00 4.118 0.176 4.8 11/01/09 39,386,813.1 278.8 1,840.02,825.6 269 60.00 4.193 0.190 4.6 11/01/09 40,813,552.8 279.4 1,840.02,928.0 275 60.00 4.173 0.196 2.8 11/01/09 39,543,614.2 275.6 1,840.02,879.8 269 60.00 3.988 0.183 3.1 11/01/09 32,341,585.5 267.9 1,840.02,267.5 210 60.00 2.487 0.090 3.8 11/01/09 29,067,884.7 269.7 1,840.0 1,990.5 191 60.00 2.771 0.088 4.5 11/01/09 33,174,530.3 272.0 1,840.02,325.9 221 60.00 3.342 0.125 4.8 11/01/09 34,455,742.9 272.1 1,840.02,396.9 231 60.00 3.988 0.153 4.9 11/01/09 36,435,879.4 274.51,840.02,574.3 243 60.00 4.262 0.175 5.1 11/01/09 35,556,399.3 273.4 1,840.02,512.1 236 60.00 4.303 0.172 5.5 11/01/09 37,002,455.3 274.7 1,840.02,614.3 247 60.00 4.478 0.187 5.1 11/01/09 37,688,256.5 274.7 1,840.02,662.7 254 60.00 4.902 0.208 4.2 11/01/09 37,699,252.3 274.0 1,840.02,643.0 249 60.00 4.504 0.190 3.9 11/01/09 31,981,894.9 267.9 1,840.02,259.6 205 60.00 3.670 0.133 4.6 11/01/09 27,281,837.6 269.1 1,840.0 1,868.2 179 60.00 3.505 0.105 4.6 11/01/09 30,494,206.9 269.1 1,840.02,121.3 202 60.00 4.110 0.139 4.4 11/01/09 29,174,384.4 267.7 1,840.02,029.5 190 60.00 4.080 0.133 4.3 11/01/09 28,103,698.9 267.3 1,840.0 1,939.8 182 60.00 3.998 0.124 4.7 11/01/09 26,120,876.6 268.8 1,840.0 1,760.3 171 60.00 4.015 0.113 4.7 11/01/09 30,108,104.9 269.6 1,840.02,094.5 196 60.00 4.235 0.141 5.1 11/01/09 29,351,723.3 269.3 1,840.02,025.9 191 60.00 4.266 0.138 5.5 10/31/09 29,136,515.7 269.8 1,840.02,011.1 193 60.00 4.581 0.148 6.2 10/31/09 30,904,790.0 274.51,840.02,149.9 209 60.00 4.966 0.171 6.3 10/31/09 37,441,575.2 279.1 1,840.02,706.4 254 60.00 5.304 0.230 6.4 10/31/09 39,911,407.9 281.0 1,840.02,884.9 273 60.00 5.440 0.251 6.8 10/31/09 39,842,284.8 281.1 1,840.02,858.2 272 60.00 5.584 0.256 6.8 10/31/09 40,136,833.1 281.0 1,840.02,901.2 275 60.00 5.910 0.274 10/31/09 39,934,806.5 279.1 1,840.02,864.9 272 60.00 5.893 0.270

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 4.0 3.7 11/03/09 40,248,265.1 277.51,840.02,909.2 274 60.00 3.407 0.159 3.4 11/03/09 39,763,127.5 277.7 1,840.02,917.4 273 60.00 3.158 0.147 3.8 11/03/09 37,204,548.6 273.9 1,840.02,709.5 249 60.00 2.886 0.125 4.2 11/03/09 33,950,310.2 273.8 1,840.02,417.1 228 60.00 3.348 0.129 3.8 11/03/09 37,995,654.2 275.4 1,840.02,767.1 261 60.00 3.583 0.159 2.9 11/03/09 39,107,657.2 274.6 1,840.02,869.3 268 60.00 3.200 0.147 4.1 11/03/09 34,559,445.1 273.51,840.02,498.0 234 60.00 2.479 0.099 4.2 11/03/09 39,504,710.9 277.8 1,840.02,877.0 271 60.00 3.509 0.162 4.3 11/03/09 40,260,375.3 278.2 1,840.02,932.0 277 60.00 3.617 0.170 4.2 11/03/09 40,134,863.3 277.7 1,840.02,922.9 275 60.00 3.696 0.173 4.4 11/03/09 40,318,345.1 277.3 1,840.02,936.2 275 60.00 3.619 0.170 4.6 11/03/09 39,829,058.7 277.2 1,840.02,878.9 272 60.00 3.819 0.176 4.1 11/03/09 39,821,097.9 275.8 1,840.02,856.7 270 60.00 3.972 0.182 2.8 11/03/09 35,628,818.4 269.7 1,840.02,575.4 234 60.00 3.507 0.144 3.2 11/03/09 26,945,444.6 264.3 1,840.0 1,918.4 180 60.00 2.457 0.076 3.2 11/03/09 25,878,696.9 266.2 1,840.0 1,800.3 172 60.00 2.907 0.083 3.2 11/03/09 27,991,945.6 268.3 1,840.0 1,947.3 189 60.00 2.891 0.090 3.2 11/03/09 30,001,708.7 268.2 1,840.02,136.0 199 60.00 2.824 0.096 3.2 11/03/09 28,107,889.0 266.1 1,840.0 1,970.6 188 60.00 2.862 0.090 3.5 11/02/09 28,080,509.1 271.2 1,840.0 1,968.7 191 60.00 2.844 0.089 4.0 11/02/09 35,387,032.3 275.4 1,840.02,557.9 240 60.00 3.006 0.123 4.4 11/02/09 38,317,357.9 277.7 1,840.02,769.7 264 60.00 3.410 0.151 4.7 11/02/09 38,612,714.1 278.7 1,840.02,770.1 263 60.00 3.832 0.170 4.3 11/02/09 40,121,505.3 280.0 1,840.02,900.1 274 60.00 4.085 0.190 3.9 11/02/09 40,304,943.0 279.2 1,840.02,957.2 275 60.00 3.638 0.172 3.4 11/02/09 39,766,651.2 278.3 1,840.02,917.7 275 60.00 3.308 0.154 2.9 11/02/09 34,475,601.7 272.51,840.02,473.3 229 60.00 2.962 0.117 3.7 11/02/09 34,127,413.3 274.7 1,840.02,448.2 231 60.00 2.571 0.100 4.2 11/02/09 37,097,975.5 278.8 1,840.02,681.5 254 60.00 3.174 0.136 4.1 11/02/09 38,743,217.3 279.4 1,840.02,821.5 267 60.00 3.589 0.162 4.1 11/02/09 40,062,890.1 279.4 1,840.02,895.9 274 60.00 3.565 0.165 4.1 11/02/09 40,457,172.5 280.0 1,840.02,902.4 272 60.00 3.516 0.164 4.2 11/02/09 40,324,436.5 280.4 1,840.02,892.8 273 60.00 3.606 0.166 4.6 11/02/09 40,186,963.5 280.51,840.02,861.1 273 60.00 3.658 0.167 4.9 11/02/09 39,849,493.0 280.7 1,840.02,858.7 272 60.00 4.037 0.184 4.8 11/02/09 40,543,814.2 279.7 1,840.02,908.6 275 60.00 4.273 0.199 11/02/09 36,418,333.9 272.6 1,840.02,592.8 237 60.00 4.200 0.174

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 C 10:00 C 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 4.4 3.4 11/05/09 40,609,578.1 276.2 1,840.02,935.4 276 60.00 3.769 0.177 2.5 11/05/09 37,334,346.4 271.1 1,840.02,698.6 248 60.00 2.894 0.125 2.9 11/05/09 30,441,461.0 266.7 1,840.02,117.6 197 60.00 2.272 0.077 3.0 11/05/09 26,537,474.4 265.8 1,840.0 1,802.8 169 60.00 2.649 0.076 2.9 11/05/09 29,322,197.7 267.4 1,840.0 1,992.0 190 60.00 2.713 0.087 2.4 11/05/09 28,755,093.8 268.2 1,840.0 1,969.1 190 60.00 2.666 0.084 2.0 11/05/09 29,952,164.8 270.2 1,840.02,099.9 198 60.00 2.095 0.070 3.3 11/05/09 31,702,677.8 271.1 1,840.02,222.7 207 60.00 1.754 0.063 4.5 11/04/09 31,801,795.9 274.7 1,840.02,212.3 212 60.00 2.926 0.104 4.7 11/04/09 38,786,412.9 278.8 1,840.02,782.5 259 60.00 3.946 0.175 4.6 11/04/09 39,791,802.9 278.8 1,840.02,854.6 268 60.00 4.049 0.185 4.4 11/04/09 40,300,987.6 278.8 1,840.02,913.1 274 60.00 4.000 0.186 4.0 11/04/09 40,654,217.5 277.8 1,840.02,938.6 277 60.00 3.821 0.179 3.9 11/04/09 40,191,551.0 277.4 1,840.02,883.3 272 60.00 3.513 0.162 3.2 11/04/09 40,699,445.7 277.51,840.02,897.6 273 60.00 3.387 0.157 3.6 11/04/09 37,999,047.0 274.7 1,840.02,726.0 253 60.00 2.818 0.123 3.8 11/04/09 37,630,733.5 275.3 1,840.02,699.6 251 60.00 3.161 0.136 3.8 11/04/09 37,039,425.9 274.8 1,840.02,677.3 250 60.00 3.299 0.141 3.8 11/04/09 37,893,346.0 275.7 1,840.02,739.0 254 60.00 3.277 0.144 4.2 11/04/09 37,056,384.4 277.0 1,840.02,678.5 248 60.00 3.321 0.142 4.4 11/04/09 38,770,099.0 279.51,840.02,802.4 262 60.00 3.615 0.162 4.6 11/04/09 39,356,245.3 279.3 1,840.02,887.5 270 60.00 3.719 0.172 4.8 11/04/09 39,696,267.4 279.2 1,840.02,890.9 272 60.00 3.963 0.184 4.1 11/04/09 39,730,870.2 279.3 1,840.02,893.5 272 60.00 4.074 0.189 3.7 11/04/09 39,657,890.1 278.7 1,840.02,909.7 271 60.00 3.471 0.161 3.3 11/04/09 38,444,198.1 273.9 1,840.02,757.9 255 60.00 3.248 0.143 3.2 11/04/09 32,060,090.6 269.8 1,840.02,247.7 212 60.00 2.928 0.106 2.9 11/04/09 29,540,987.6 267.2 1,840.02,039.0 189 60.00 2.903 0.094 3.0 11/04/09 28,050,235.4 266.7 1,840.0 1,905.6 178 60.00 2.701 0.082 3.4 11/04/09 27,811,881.1 267.8 1,840.0 1,874.3 179 60.00 2.776 0.083 3.3 11/04/09 29,368,101.0 268.9 1,840.02,059.0 193 60.00 3.066 0.101 2.4 11/04/09 30,720,881.1 269.2 1,840.02,187.2 203 60.00 2.882 0.101 3.0 11/03/09 29,249,315.4 270.7 1,840.02,066.5 196 60.00 2.125 0.070 3.9 11/03/09 35,372,053.0 276.6 1,840.02,479.9 236 60.00 2.708 0.107 3.8 11/03/09 39,542,841.3 278.3 1,840.02,858.3 268 60.00 3.376 0.154 3.8 11/03/09 39,639,439.0 277.8 1,840.02,886.8 271 60.00 3.210 0.148 11/03/09 39,498,575.5 276.6 1,840.02,898.0 271 60.00 3.199 0.149

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 4.3 4.3 11/06/09 38,736,738.3 281.4 1,840.02,821.1 262 60.00 3.683 0.166 4.4 11/06/09 39,485,806.2 280.4 1,840.02,875.6 270 60.00 3.719 0.171 4.5 11/06/09 39,473,608.7 279.6 1,840.02,874.7 268 60.00 3.785 0.174 4.5 11/06/09 40,765,620.4 281.1 1,840.02,924.5 274 60.00 3.955 0.185 4.0 11/06/09 38,223,397.2 274.7 1,840.02,700.5 250 60.00 3.968 0.171 3.9 11/06/09 32,219,698.2 274.0 1,840.02,258.9 210 60.00 3.522 0.127 4.1 11/06/09 36,533,561.4 276.8 1,840.02,640.8 243 60.00 3.393 0.143 3.9 11/06/09 36,902,671.5 278.2 1,840.02,667.4 248 60.00 3.550 0.152 3.9 11/06/09 37,507,180.8 277.8 1,840.02,711.1 250 60.00 3.398 0.147 4.2 11/06/09 38,208,562.8 279.1 1,840.02,761.8 256 60.00 3.404 0.150 4.1 11/06/09 36,741,540.7 276.0 1,840.02,675.8 246 60.00 3.638 0.155 4.0 11/06/09 36,733,906.6 277.8 1,840.02,675.2 249 60.00 3.534 0.151 3.7 11/06/09 39,743,583.0 277.7 1,840.02,916.0 272 60.00 3.358 0.157 2.9 11/06/09 40,807,453.2 277.7 1,840.02,949.6 276 60.00 3.236 0.152 2.1 11/06/09 34,384,554.2 267.0 1,840.02,448.1 224 60.00 2.531 0.099 1.9 11/06/09 25,530,234.5 263.7 1,840.0 1,803.8 166 60.00 1.817 0.052 2.0 11/06/09 25,118,855.9 263.1 1,840.0 1,774.7 160 60.00 1.644 0.047 2.0 11/06/09 23,983,906.0 263.3 1,840.0 1,668.5 151 60.00 1.755 0.047 2.2 11/06/09 23,736,903.9 263.3 1,840.0 1,625.5 149 60.00 1.783 0.046 3.1 11/06/09 23,525,065.4 264.3 1,840.0 1,674.9 150 60.00 1.929 0.052 2.8 11/06/09 24,813,486.1 266.0 1,840.0 1,712.6 159 60.00 2.764 0.076 2.8 11/05/09 25,921,773.4 266.1 1,840.0 1,789.2 164 60.00 2.548 0.073 3.8 11/05/09 25,414,151.1 271.1 1,840.0 1,767.9 172 60.00 2.482 0.070 4.3 11/05/09 35,464,699.0 278.7 1,840.02,602.1 241 60.00 3.198 0.133 4.6 11/05/09 39,765,265.1 281.6 1,840.02,874.3 269 60.00 3.710 0.171 4.8 11/05/09 40,114,335.2 282.8 1,840.02,921.3 271 60.00 3.957 0.185 4.5 11/05/09 40,414,518.9 284.0 1,840.02,943.3 273 60.00 4.124 0.195 4.3 11/05/09 40,558,575.4 283.8 1,840.02,975.8 277 60.00 3.829 0.183 3.9 11/05/09 39,110,406.4 279.7 1,840.02,848.2 265 60.00 3.665 0.167 4.1 11/05/09 38,088,274.6 278.3 1,840.02,753.1 256 60.00 3.343 0.147 4.5 11/05/09 38,412,071.1 278.4 1,840.02,776.5 259 60.00 3.560 0.158 4.7 11/05/09 39,702,792.4 280.3 1,840.02,891.4 267 60.00 3.850 0.177 4.6 11/05/09 39,600,844.1 280.0 1,840.02,884.0 267 60.00 4.031 0.186 5.1 11/05/09 39,959,896.9 281.1 1,840.02,888.4 268 60.00 3.997 0.185 5.0 11/05/09 40,728,090.1 281.7 1,840.02,966.1 277 60.00 4.396 0.208 4.7 11/05/09 40,065,430.9 280.7 1,840.02,896.0 274 60.00 4.326 0.200 11/05/09 40,490,692.9 278.3 1,840.02,948.8 275 60.00 4.014 0.189

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 3.2 2.9 11/08/09 24,047,453.2 262.0 1,840.0 1,659.8 155 60.00 2.875 0.076 2.6 11/08/09 24,149,584.6 261.1 1,840.0 1,666.9 156 60.00 2.636 0.070 2.4 11/08/09 23,396,972.0 260.7 1,840.0 1,602.2 150 60.00 2.341 0.060 2.4 11/08/09 24,271,169.0 261.7 1,840.0 1,701.6 160 60.00 2.161 0.059 2.2 11/08/09 23,451,142.6 261.3 1,840.0 1,644.1 152 60.00 2.169 0.057 2.4 11/08/09 24,473,628.5 262.9 1,840.0 1,689.2 157 60.00 1.977 0.053 2.9 11/08/09 25,631,432.0 262.8 1,840.0 1,797.0 164 60.00 2.149 0.062 2.9 11/08/09 24,201,653.2 262.8 1,840.0 1,617.9 150 60.00 2.746 0.071 2.8 11/08/09 24,660,982.5 263.0 1,840.0 1,675.3 156 60.00 2.651 0.071 3.2 11/08/09 24,720,454.2 265.8 1,840.0 1,719.7 162 60.00 2.553 0.070 3.2 11/07/09 26,357,702.8 264.9 1,840.0 1,862.3 173 60.00 2.776 0.083 3.6 11/07/09 25,420,131.0 265.6 1,840.0 1,782.2 168 60.00 2.860 0.082 4.0 11/07/09 26,423,491.9 266.8 1,840.0 1,866.8 175 60.00 3.160 0.094 4.2 11/07/09 27,160,821.9 266.7 1,840.0 1,904.2 178 60.00 3.530 0.108 4.0 11/07/09 27,288,233.4 266.4 1,840.0 1,898.3 177 60.00 3.762 0.114 3.9 11/07/09 27,101,830.7 268.4 1,840.0 1,855.9 175 60.00 3.610 0.107 3.8 11/07/09 27,659,192.5 267.9 1,840.0 1,894.0 180 60.00 3.588 0.109 3.7 11/07/09 27,643,823.6 267.7 1,840.0 1,893.0 180 60.00 3.417 0.103 3.3 11/07/09 27,483,500.3 267.4 1,840.0 1,897.0 179 60.00 3.388 0.103 3.2 11/07/09 27,714,113.4 268.0 1,840.0 1,912.9 182 60.00 3.021 0.092 3.0 11/07/09 28,078,041.4 268.6 1,840.0 1,938.0 181 60.00 2.879 0.089 2.5 11/07/09 28,009,542.3 268.8 1,840.0 1,918.1 180 60.00 2.765 0.085 3.0 11/07/09 28,431,620.1 268.3 1,840.0 1,931.5 179 60.00 2.331 0.072 3.1 11/07/09 26,483,772.0 267.7 1,840.0 1,828.0 173 60.00 2.736 0.080 2.7 11/07/09 27,660,916.8 267.4 1,840.0 1,909.2 180 60.00 2.840 0.087 2.8 11/07/09 27,135,523.7 265.9 1,840.0 1,858.2 176 60.00 2.464 0.073 2.6 11/07/09 25,586,336.3 264.51,840.0 1,738.2 164 60.00 2.566 0.071 2.5 11/07/09 25,562,381.9 264.0 1,840.0 1,736.5 162 60.00 2.386 0.066 3.0 11/07/09 25,326,347.1 265.2 1,840.0 1,734.3 161 60.00 2.280 0.063 2.8 11/07/09 25,784,142.6 265.3 1,840.0 1,751.6 162 60.00 2.714 0.076 2.8 11/07/09 24,323,449.6 265.51,840.0 1,639.2 152 60.00 2.626 0.069 2.6 11/07/09 24,163,795.7 265.4 1,840.0 1,654.7 153 60.00 2.535 0.067 2.1 11/07/09 24,536,400.7 264.7 1,840.0 1,706.9 157 60.00 2.337 0.064 2.5 11/07/09 23,349,120.5 265.3 1,840.0 1,611.6 149 60.00 1.875 0.048 3.1 11/06/09 24,273,795.9 267.3 1,840.0 1,688.6 154 60.00 2.283 0.061 3.8 11/06/09 28,075,154.2 272.7 1,840.0 1,953.0 185 60.00 2.765 0.086 11/06/09 35,939,014.6 279.1 1,840.02,558.7 241 60.00 3.343 0.137

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 3.2 3.2 11/09/09 30,509,068.2 267.4 1,840.02,188.7 207 60.00 2.745 0.096 3.6 11/09/09 31,530,486.1 267.51,840.02,261.9 215 60.00 2.819 0.102 2.9 11/09/09 31,775,032.3 267.8 1,840.02,296.8 218 60.00 3.120 0.114 2.6 11/09/09 32,271,382.4 268.6 1,840.02,332.6 218 60.00 2.515 0.094 2.9 11/09/09 31,367,287.1 269.2 1,840.02,267.3 212 60.00 2.239 0.081 3.4 11/09/09 31,984,054.6 269.51,840.02,294.5 214 60.00 2.522 0.092 2.9 11/09/09 31,800,694.4 267.9 1,840.02,298.7 216 60.00 2.967 0.109 1.8 11/09/09 30,991,494.1 265.51,840.02,240.1 209 60.00 2.544 0.091 1.7 11/09/09 26,948,020.3 263.9 1,840.0 1,933.2 178 60.00 1.585 0.049 1.7 11/09/09 27,359,505.6 264.4 1,840.0 1,888.4 179 60.00 1.526 0.046 2.2 11/09/09 27,684,219.5 265.3 1,840.0 1,925.8 181 60.00 1.525 0.047 2.3 11/09/09 26,985,345.5 264.8 1,840.0 1,935.9 181 60.00 1.938 0.060 2.0 11/09/09 26,491,786.0 262.9 1,840.0 1,914.9 175 60.00 2.024 0.062 2.1 11/09/09 26,548,436.9 264.1 1,840.0 1,846.8 176 60.00 1.836 0.054 3.0 11/09/09 28,064,498.6 264.3 1,840.0 1,937.0 182 60.00 1.915 0.060 3.3 11/09/09 27,694,635.9 265.0 1,840.0 1,896.5 178 60.00 2.741 0.083 3.5 11/09/09 28,020,367.7 264.6 1,840.0 1,964.4 180 60.00 2.969 0.093 3.2 11/09/09 26,904,174.3 263.7 1,840.0 1,871.6 175 60.00 3.169 0.095 3.2 11/09/09 25,970,788.0 264.51,840.0 1,834.9 168 60.00 2.834 0.083 3.4 11/09/09 25,108,137.8 263.6 1,840.0 1,719.4 158 60.00 2.935 0.081 2.6 11/09/09 27,352,927.0 263.8 1,840.0 1,843.4 171 60.00 3.097 0.092 2.4 11/09/09 24,698,105.2 262.9 1,840.0 1,677.9 157 60.00 2.442 0.065 3.7 11/09/09 25,517,736.9 263.4 1,840.0 1,775.2 164 60.00 2.163 0.061 3.5 11/08/09 27,357,594.1 265.1 1,840.0 1,903.2 179 60.00 3.355 0.102 3.2 11/08/09 27,886,148.4 267.4 1,840.0 1,939.9 186 60.00 3.100 0.096 2.9 11/08/09 34,399,287.0 272.7 1,840.02,486.4 237 60.00 2.731 0.109 3.0 11/08/09 38,418,583.3 276.1 1,840.02,818.8 264 60.00 2.481 0.112 2.8 11/08/09 39,451,916.5 275.9 1,840.02,894.6 269 60.00 2.561 0.118 2.3 11/08/09 38,772,045.0 273.7 1,840.02,802.5 262 60.00 2.436 0.109 1.9 11/08/09 32,803,467.7 252.9 1,840.02,299.8 210 60.00 2.050 0.075 2.0 11/08/09 24,477,877.6 245.8 1,840.0 1,636.3 155 60.00 1.782 0.047 2.1 11/08/09 24,915,562.1 247.7 1,840.0 1,638.5 156 60.00 1.862 0.049 2.3 11/08/09 25,153,006.7 253.51,840.0 1,626.7 157 60.00 1.992 0.052 2.8 11/08/09 25,198,206.6 260.7 1,840.0 1,657.0 157 60.00 2.145 0.057 2.5 11/08/09 24,787,309.4 252.0 1,840.0 1,670.4 157 60.00 2.568 0.068 2.8 11/08/09 24,955,183.7 246.1 1,840.0 1,641.1 158 60.00 2.345 0.061 11/08/09 24,392,270.9 258.4 1,840.0 1,657.1 157 60.00 2.611 0.069

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 ST ST STC 13:00 ST ST STC 14:00 ST ST STC 15:00 ST ST STC 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C 06:00 07:00 08:00 09:00 10:00 11:00 2.8 2.4 11/11/09 23,453,535.6 260.4 1,840.0 1,631.6 148 60.00 2.546 0.066 2.4 11/11/09 23,817,601.5 261.4 1,840.0 1,605.1 149 60.00 2.204 0.056 2.3 11/11/09 23,672,111.7 262.1 1,840.0 1,646.7 148 60.00 2.120 0.056 2.5 11/11/09 23,894,513.6 262.1 1,840.0 1,662.3 148 60.00 2.058 0.055 2.5 11/11/09 23,607,935.9 261.3 1,840.0 1,642.3 149 60.00 2.278 0.060 2.7 11/11/09 22,905,716.7 263.6 1,840.0 1,581.0 148 60.00 2.263 0.057 3.0 11/11/09 29,084,772.3 268.3 1,840.02,023.3 194 60.00 2.425 0.079 3.1 11/11/09 29,687,270.5 267.4 1,840.02,081.3 195 60.00 2.682 0.090 3.0 11/11/09 32,342,596.3 269.6 1,840.02,285.1 214 60.00 2.741 0.100 2.5 11/11/09 30,530,445.7 265.7 1,840.02,140.4 201 60.00 2.638 0.090 2.3 11/11/09 29,111,761.9 266.9 1,840.02,041.0 194 60.00 2.215 0.072 2.7 11/11/09 32,021,442.4 268.6 1,840.02,314.6 216 60.00 1.938 0.072 2.6 11/10/09 29,679,356.6 267.3 1,840.02,113.0 200 60.00 2.385 0.081 2.6 11/10/09 32,271,157.2 269.9 1,840.02,350.2 218 60.00 2.220 0.084 2.4 11/10/09 32,482,908.1 270.2 1,840.02,330.3 216 60.00 2.229 0.083 2.7 11/10/09 32,640,941.3 270.51,840.02,341.6 218 60.00 2.112 0.079 3.3 11/10/09 32,662,675.1 271.3 1,840.02,361.0 218 60.00 2.361 0.089 3.5 11/10/09 32,046,632.4 275.0 1,840.02,333.9 218 60.00 2.854 0.106 3.4 11/10/09 31,864,329.2 275.2 1,840.02,320.5 218 60.00 2.994 0.111 3.4 11/10/09 32,116,159.2 272.4 1,840.02,356.3 218 60.00 2.938 0.110 3.4 11/10/09 30,601,512.8 273.8 1,840.02,212.0 207 60.00 2.899 0.103 3.4 11/10/09 31,801,123.1 276.7 1,840.02,315.9 214 60.00 2.890 0.107 3.4 11/10/09 32,803,361.2 277.2 1,840.02,388.9 220 60.00 2.883 0.110 3.3 11/10/09 33,823,444.2 276.2 1,840.02,463.2 226 60.00 2.878 0.113 3.5 11/10/09 32,289,732.1 275.6 1,840.02,316.5 219 60.00 2.852 0.106 3.6 11/10/09 32,755,584.5 276.9 1,840.02,367.7 221 60.00 3.013 0.114 3.0 11/10/09 33,358,895.0 274.2 1,840.02,429.4 222 60.00 3.075 0.119 3.0 11/10/09 32,165,677.2 270.1 1,840.02,290.1 213 60.00 2.654 0.098 2.5 11/10/09 31,211,790.0 267.6 1,840.02,222.2 211 60.00 2.609 0.093 2.7 11/10/09 31,030,009.7 267.9 1,840.02,226.1 212 60.00 2.158 0.077 2.3 11/10/09 31,939,939.3 268.9 1,840.02,308.7 216 60.00 2.353 0.087 2.5 11/10/09 30,620,049.8 267.1 1,840.02,213.3 203 60.00 1.987 0.070 3.0 11/10/09 29,183,098.9 265.3 1,840.02,093.6 191 60.00 2.192 0.073 2.8 11/10/09 26,460,116.9 264.9 1,840.0 1,869.5 178 60.00 2.667 0.079 2.8 11/10/09 28,939,120.3 267.6 1,840.02,076.1 194 60.00 2.405 0.080 3.0 11/10/09 28,457,991.0 271.3 1,840.02,041.6 191 60.00 2.444 0.080 11/09/09 31,401,105.1 268.0 1,840.02,252.7 207 60.00 2.633 0.095

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 2.4 2.8 11/13/09 24,938,299.9 265.3 1,840.0 1,734.8 167 60.00 2.136 0.059 3.2 11/12/09 25,778,846.9 266.3 1,840.0 1,807.3 174 60.00 2.529 0.073 3.2 11/12/09 29,075,921.5 269.2 1,840.02,085.9 200 60.00 2.765 0.092 3.4 11/12/09 30,497,116.8 270.3 1,840.02,187.8 206 60.00 2.781 0.097 3.4 11/12/09 31,517,156.2 270.6 1,840.02,261.0 212 60.00 2.934 0.106 3.4 11/12/09 31,510,775.5 270.8 1,840.02,243.4 211 60.00 2.992 0.107 3.5 11/12/09 31,843,520.5 270.1 1,840.02,284.5 218 60.00 2.987 0.109 3.4 11/12/09 32,688,991.5 269.4 1,840.02,309.5 221 60.00 3.084 0.114 3.4 11/12/09 32,307,935.5 269.6 1,840.02,230.0 215 60.00 3.065 0.110 3.5 11/12/09 32,628,274.3 271.0 1,840.02,287.5 218 60.00 3.050 0.111 3.3 11/12/09 33,746,715.7 271.51,840.02,384.3 225 60.00 3.083 0.118 3.1 11/12/09 33,520,537.0 269.1 1,840.02,331.9 222 60.00 2.947 0.110 3.1 11/12/09 30,479,522.5 267.3 1,840.02,170.0 205 60.00 2.723 0.094 3.3 11/12/09 30,020,265.1 267.1 1,840.02,137.3 202 60.00 2.752 0.094 3.4 11/12/09 29,837,478.1 267.9 1,840.02,140.5 202 60.00 2.918 0.100 3.4 11/12/09 30,242,702.2 268.51,840.02,169.6 202 60.00 2.976 0.103 3.5 11/12/09 30,235,977.6 268.2 1,840.02,185.5 200 60.00 2.947 0.103 3.4 11/12/09 29,947,391.5 268.1 1,840.02,164.6 198 60.00 2.983 0.103 3.3 11/12/09 29,405,260.5 265.4 1,840.02,109.5 195 60.00 2.922 0.098 3.1 11/12/09 26,256,475.8 267.51,840.0 1,855.0 177 60.00 2.889 0.086 3.3 11/12/09 30,388,919.3 267.6 1,840.02,180.1 200 60.00 2.745 0.095 3.4 11/12/09 27,731,256.2 266.2 1,840.0 1,959.3 181 60.00 2.882 0.090 3.6 11/12/09 28,791,831.1 267.51,840.02,018.6 189 60.00 3.071 0.099 3.3 11/12/09 30,038,758.5 266.7 1,840.02,138.6 201 60.00 3.131 0.107 3.1 11/12/09 27,992,880.8 265.1 1,840.0 1,962.6 186 60.00 2.980 0.093 3.1 11/11/09 29,336,784.0 266.9 1,840.02,056.8 200 60.00 2.786 0.092 3.2 11/11/09 31,158,718.9 267.1 1,840.02,218.4 212 60.00 2.678 0.095 2.8 11/11/09 30,860,491.0 267.4 1,840.02,213.9 212 60.00 2.799 0.099 2.7 11/11/09 32,702,466.5 268.7 1,840.02,363.8 222 60.00 2.401 0.091 2.8 11/11/09 32,431,195.8 269.7 1,840.02,308.9 218 60.00 2.331 0.086 3.1 11/11/09 32,747,061.8 270.3 1,840.02,384.8 220 60.00 2.435 0.093 3.0 11/11/09 32,530,378.6 269.2 1,840.02,369.0 221 60.00 2.639 0.100 2.8 11/11/09 32,947,243.7 267.51,840.02,345.7 222 60.00 2.611 0.098 2.2 11/11/09 32,562,445.9 266.3 1,840.02,318.3 214 60.00 2.493 0.092 2.5 11/11/09 25,931,269.7 261.8 1,840.0 1,761.6 162 60.00 2.015 0.057 2.8 11/11/09 23,556,717.0 262.3 1,840.0 1,638.7 148 60.00 2.201 0.058 11/11/09 23,606,851.5 260.9 1,840.0 1,655.1 149 60.00 2.451 0.065

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 3.5 3.4 11/14/09 32,378,997.0 270.2 1,840.02,340.4 217 60.00 2.997 0.112 3.4 11/14/09 31,568,902.6 270.4 1,840.02,281.9 214 60.00 2.931 0.107 3.5 11/14/09 32,203,836.9 270.7 1,840.02,310.3 217 60.00 2.942 0.108 3.6 11/14/09 32,514,269.9 271.1 1,840.02,332.5 218 60.00 3.081 0.115 3.6 11/14/09 31,978,012.4 270.1 1,840.02,294.1 215 60.00 3.104 0.113 3.6 11/14/09 31,533,058.5 269.1 1,840.02,245.0 214 60.00 3.188 0.114 3.4 11/14/09 31,363,844.0 268.51,840.02,215.9 213 60.00 3.194 0.113 3.1 11/14/09 30,933,014.2 267.9 1,840.02,168.7 210 60.00 3.037 0.106 3.1 11/14/09 30,604,755.8 268.2 1,840.02,162.3 205 60.00 2.739 0.094 3.2 11/14/09 30,630,569.7 268.6 1,840.02,147.5 205 60.00 2.740 0.094 3.0 11/14/09 30,963,397.0 269.0 1,840.02,153.9 205 60.00 2.892 0.100 3.1 11/14/09 30,921,047.5 267.0 1,840.02,151.0 200 60.00 2.698 0.093 3.2 11/14/09 27,917,455.1 266.8 1,840.0 1,942.1 187 60.00 2.777 0.086 3.1 11/14/09 29,895,513.9 267.6 1,840.02,112.2 202 60.00 2.851 0.097 2.9 11/13/09 29,806,786.6 266.8 1,840.02,105.9 201 60.00 2.759 0.093 3.0 11/13/09 30,702,326.8 267.51,840.02,169.2 207 60.00 2.543 0.088 2.9 11/13/09 31,931,623.5 268.0 1,840.02,221.4 212 60.00 2.663 0.094 2.8 11/13/09 32,268,501.7 268.0 1,840.02,227.3 212 60.00 2.626 0.093 3.0 11/13/09 31,999,698.8 267.8 1,840.02,208.7 210 60.00 2.542 0.090 3.1 11/13/09 31,348,027.8 267.2 1,840.02,180.7 210 60.00 2.718 0.095 2.9 11/13/09 31,796,238.9 267.1 1,840.02,194.6 213 60.00 2.812 0.099 3.0 11/13/09 32,232,559.6 268.0 1,840.02,259.8 215 60.00 2.592 0.094 3.0 11/13/09 31,938,806.9 269.0 1,840.02,256.6 213 60.00 2.651 0.096 3.0 11/13/09 33,309,272.2 269.8 1,840.02,317.1 216 60.00 2.733 0.101 3.0 11/13/09 31,908,082.9 267.51,840.02,237.0 212 60.00 2.649 0.095 3.1 11/13/09 31,569,800.9 268.3 1,840.02,196.2 212 60.00 2.692 0.094 3.2 11/13/09 31,835,218.6 268.7 1,840.02,197.3 212 60.00 2.829 0.100 3.1 11/13/09 32,018,202.0 269.3 1,840.02,279.5 213 60.00 2.762 0.101 3.2 11/13/09 31,756,611.8 269.0 1,840.02,278.2 212 60.00 2.683 0.098 3.2 11/13/09 31,957,942.0 269.51,840.02,292.6 213 60.00 2.795 0.103 2.7 11/13/09 31,696,196.7 269.6 1,840.02,273.8 211 60.00 2.830 0.103 2.7 11/13/09 31,623,547.2 266.51,840.02,251.5 206 60.00 2.374 0.085 3.0 11/13/09 24,831,352.3 266.0 1,840.0 1,713.9 162 60.00 2.477 0.068 3.0 11/13/09 27,551,019.4 266.2 1,840.0 1,916.6 178 60.00 2.684 0.082 3.5 11/13/09 25,999,177.8 265.8 1,840.0 1,794.5 167 60.00 2.751 0.079 2.7 11/13/09 25,650,507.5 265.8 1,840.0 1,756.5 171 60.00 3.184 0.089 11/13/09 26,134,900.3 264.0 1,840.0 1,846.5 171 60.00 2.362 0.070

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 4.0 4.2 11/16/09 26,459,238.8 269.7 1,840.0 1,797.5 174 60.00 3.664 0.105 4.1 11/16/09 30,238,207.4 270.6 1,840.02,169.2 204 60.00 3.690 0.128 4.0 11/16/09 29,127,142.8 270.9 1,840.02,089.5 200 60.00 3.609 0.120 4.4 11/15/09 29,435,057.4 270.9 1,840.02,111.6 201 60.00 3.444 0.117 4.5 11/15/09 35,123,232.5 276.4 1,840.02,481.5 238 60.00 3.883 0.154 4.6 11/15/09 37,653,249.6 278.6 1,840.02,701.2 256 60.00 3.955 0.171 4.8 11/15/09 39,731,030.6 279.8 1,840.02,893.5 272 60.00 3.927 0.182 4.8 11/15/09 39,336,010.1 279.6 1,840.02,864.7 270 60.00 4.140 0.190 4.4 11/15/09 39,126,037.4 278.3 1,840.02,849.4 267 60.00 4.107 0.187 4.2 11/15/09 39,288,988.8 277.2 1,840.02,861.3 267 60.00 3.816 0.174 4.1 11/15/09 34,653,408.4 272.6 1,840.02,486.0 231 60.00 3.654 0.145 4.0 11/15/09 33,799,569.1 273.4 1,840.02,388.0 226 60.00 3.598 0.138 3.9 11/15/09 33,901,577.8 273.7 1,840.02,376.8 225 60.00 3.537 0.135 3.4 11/15/09 35,202,295.1 272.0 1,840.02,525.4 235 60.00 3.393 0.137 3.9 11/15/09 32,040,710.1 270.4 1,840.02,281.2 214 60.00 3.015 0.110 3.6 11/15/09 31,975,133.5 270.3 1,840.02,328.6 213 60.00 3.315 0.123 3.8 11/15/09 31,509,916.8 268.51,840.02,277.6 212 60.00 3.070 0.112 3.9 11/15/09 31,015,832.6 268.2 1,840.02,241.9 210 60.00 3.284 0.118 3.9 11/15/09 31,354,659.8 266.3 1,840.02,249.4 210 60.00 3.422 0.123 3.4 11/15/09 32,048,432.0 260.2 1,840.02,299.1 213 60.00 3.383 0.124 3.3 11/15/09 28,775,139.8 252.8 1,840.02,033.0 188 60.00 2.972 0.097 3.1 11/15/09 25,833,373.3 254.4 1,840.0 1,811.1 172 60.00 2.924 0.085 3.3 11/15/09 27,539,336.6 254.7 1,840.0 1,945.7 180 60.00 2.711 0.085 3.3 11/15/09 25,941,921.7 256.7 1,840.0 1,790.6 169 60.00 3.017 0.086 3.5 11/15/09 26,853,941.9 257.4 1,840.0 1,868.1 176 60.00 2.967 0.089 3.5 11/15/09 27,343,462.2 256.1 1,840.0 1,931.8 181 60.00 3.104 0.096 3.7 11/15/09 25,143,917.7 260.9 1,840.0 1,749.1 170 60.00 3.154 0.088 3.5 11/14/09 29,168,915.2 262.8 1,840.02,076.7 196 60.00 3.273 0.109 3.2 11/14/09 29,574,671.0 267.6 1,840.02,089.5 200 60.00 3.057 0.102 3.4 11/14/09 30,988,636.8 270.1 1,840.02,189.4 207 60.00 2.854 0.100 3.5 11/14/09 31,365,973.7 271.6 1,840.02,233.1 209 60.00 2.985 0.107 3.7 11/14/09 31,552,591.7 271.2 1,840.02,246.4 210 60.00 3.067 0.110 3.6 11/14/09 31,510,874.6 269.9 1,840.02,260.6 213 60.00 3.244 0.118 3.4 11/14/09 31,389,032.6 268.9 1,840.02,234.8 213 60.00 3.168 0.114 3.5 11/14/09 31,129,209.9 269.1 1,840.02,216.2 211 60.00 2.995 0.106 3.4 11/14/09 32,179,470.1 270.2 1,840.02,326.0 216 60.00 2.995 0.111 11/14/09 32,017,156.8 270.51,840.02,296.9 215 60.00 3.003 0.110

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C S S S 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 3.9 4.7 11/17/09 40,336,422.7 279.0 1,840.02,959.4 279 60.00 3.345 0.158 4.9 11/17/09 40,112,290.5 279.1 1,840.02,964.8 278 60.00 3.994 0.189 4.8 11/17/09 39,824,455.2 280.1 1,840.02,943.5 276 60.00 4.156 0.195 4.9 11/17/09 39,792,611.2 280.8 1,840.02,941.2 277 60.00 4.075 0.192 4.7 11/17/09 40,252,507.6 281.1 1,840.02,997.1 282 60.00 4.116 0.198 4.8 11/17/09 40,068,317.9 280.4 1,840.02,983.3 279 60.00 3.992 0.190 5.2 11/17/09 40,110,648.7 280.3 1,840.02,964.7 280 60.00 4.063 0.193 5.4 11/17/09 40,316,458.5 279.51,840.03,001.8 280 60.00 4.394 0.210 4.3 11/17/09 39,728,613.7 275.8 1,840.02,936.5 272 60.00 4.537 0.212 3.7 11/17/09 31,393,100.0 264.51,840.02,286.2 207 60.00 3.648 0.134 3.6 11/17/09 24,899,695.8 261.7 1,840.0 1,732.2 160 60.00 3.322 0.092 3.4 11/17/09 24,003,414.4 257.1 1,840.0 1,656.7 154 60.00 3.226 0.086 3.7 11/17/09 24,914,350.3 243.9 1,840.0 1,719.6 159 60.00 3.095 0.085 3.7 11/17/09 24,698,514.5 242.8 1,840.0 1,677.9 156 60.00 3.399 0.091 3.7 11/17/09 24,422,213.7 246.51,840.0 1,685.6 160 60.00 3.363 0.090 4.0 11/17/09 26,998,044.3 250.4 1,840.0 1,863.4 180 60.00 3.348 0.100 4.9 11/16/09 26,935,073.0 257.8 1,840.0 1,873.7 178 60.00 3.555 0.107 5.3 11/16/09 31,524,034.9 269.51,840.02,227.2 215 60.00 4.329 0.154 4.9 11/16/09 36,694,107.9 271.7 1,840.02,612.5 246 60.00 4.615 0.193 5.4 11/16/09 35,695,114.3 272.0 1,840.02,560.7 240 60.00 4.259 0.174 5.3 11/16/09 38,893,482.0 277.7 1,840.02,769.0 260 60.00 4.724 0.209 4.9 11/16/09 39,470,382.3 277.9 1,840.02,895.9 270 60.00 4.485 0.208 3.9 11/16/09 38,429,646.0 274.4 1,840.02,840.5 265 60.00 4.158 0.189 4.2 11/16/09 29,650,699.8 267.0 1,840.02,127.1 197 60.00 3.433 0.116 4.3 11/16/09 28,006,938.4 266.6 1,840.0 1,963.5 185 60.00 3.745 0.118 4.5 11/16/09 26,655,248.8 267.4 1,840.0 1,883.2 179 60.00 3.774 0.114 4.3 11/16/09 28,217,869.4 265.9 1,840.02,024.3 190 60.00 3.907 0.127 4.6 11/16/09 27,261,932.5 269.51,840.0 1,881.7 181 60.00 3.922 0.118 4.5 11/16/09 30,572,385.8 272.2 1,840.02,160.0 205 60.00 4.084 0.141 4.4 11/16/09 34,797,695.1 276.0 1,840.02,477.5 231 60.00 3.908 0.155 4.5 11/16/09 35,574,266.9 277.7 1,840.02,532.7 239 60.00 3.845 0.156 4.4 11/16/09 35,722,343.5 279.1 1,840.02,601.5 243 60.00 3.857 0.161 3.2 11/16/09 33,494,201.5 280.3 1,840.02,421.0 227 60.00 3.773 0.146 3.2 11/16/09 29,027,749.9 271.7 1,840.02,082.4 190 60.00 2.817 0.094 3.1 11/16/09 24,312,033.7 266.4 1,840.0 1,664.8 156 60.00 2.890 0.077 3.3 11/16/09 25,373,437.7 264.7 1,840.0 1,723.7 161 60.00 2.853 0.078 11/16/09 23,899,653.5 266.2 1,840.0 1,597.7 151 60.00 3.030 0.078

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 02:00 C 03:00 04:00 C 3.8 3.4 11/19/09 30,709,883.8 266.7 1,840.02,103.0 199 60.00 3.419 0.115 1.9 11/19/09 29,646,175.3 261.2 1,840.02,046.2 191 60.00 3.068 0.101 0.5 11/19/09 22,181,032.1 240.9 1,840.0 1,289.9 113 60.00 2.023 0.042 0.8 11/19/09 22,472,815.8 237.0 1,840.0 342.0 21 40.00 1.900 0.007 1.1 11/19/09 26,490,543.9 246.0 1,840.0 1,065.4 85 57.00 1.194 0.019 3.0 11/18/09 30,861,819.0 254.7 1,840.0 889.0 63 33.00 2.318 0.018 3.8 11/18/09 27,742,407.5 272.7 1,840.0 1,975.1 191 60.00 2.591 0.082 4.0 11/18/09 38,345,320.9 277.0 1,840.02,792.5 265 60.00 3.292 0.147 2.5 11/18/09 40,096,764.7 278.51,840.02,920.1 278 60.00 3.433 0.160 2.3 11/18/09 40,916,911.5 279.3 1,840.02,957.6 282 60.00 2.157 0.102 2.0 11/18/09 41,404,630.5 279.3 1,840.02,992.9 282 60.00 2.023 0.097 4.0 11/18/09 40,395,800.8 278.0 1,840.02,963.8 282 60.00 1.696 0.080 2.3 11/18/09 40,498,205.8 278.1 1,840.02,949.3 280 60.00 3.394 0.160 2.9 11/18/09 39,940,031.9 277.51,840.02,887.0 275 60.00 2.010 0.093 4.6 11/18/09 39,772,222.4 278.6 1,840.02,831.6 267 60.00 2.558 0.116 4.8 11/18/09 40,362,954.2 278.7 1,840.02,939.5 281 60.00 3.938 0.186 4.9 11/18/09 40,387,364.2 279.7 1,840.02,963.2 280 60.00 4.054 0.193 5.1 11/18/09 40,434,614.9 280.1 1,840.02,966.7 279 60.00 4.164 0.197 5.4 11/18/09 41,180,948.9 280.3 1,840.03,021.4 282 60.00 4.380 0.211 5.5 11/18/09 40,768,607.5 278.9 1,840.02,924.7 281 60.00 4.724 0.221 5.3 11/18/09 40,831,910.0 278.4 1,840.02,951.4 282 60.00 4.736 0.223 4.3 11/18/09 40,743,818.4 277.0 1,840.02,945.1 280 60.00 4.582 0.217 3.4 11/18/09 34,331,144.1 266.9 1,840.02,537.5 230 60.00 3.647 0.148 3.1 11/18/09 26,209,999.9 264.0 1,840.0 1,837.5 172 60.00 3.020 0.089 3.5 11/18/09 25,477,638.2 263.2 1,840.0 1,772.4 165 60.00 2.800 0.080 2.8 11/18/09 24,321,038.7 263.6 1,840.0 1,652.2 155 60.00 3.171 0.084 3.2 11/18/09 27,041,092.3 263.7 1,840.0 1,822.3 174 60.00 2.626 0.077 3.5 11/18/09 23,397,876.7 264.51,840.0 1,627.7 151 60.00 2.883 0.075 3.6 11/18/09 26,706,810.2 266.51,840.0 1,857.9 175 60.00 3.150 0.093 4.0 11/17/09 29,069,553.4 268.3 1,840.02,038.1 190 60.00 3.198 0.104 4.4 11/17/09 29,304,490.9 272.4 1,840.02,086.3 202 60.00 3.533 0.118 4.4 11/17/09 36,764,805.6 276.8 1,840.02,677.5 253 60.00 3.716 0.160 4.6 11/17/09 39,578,743.4 279.51,840.02,903.9 274 60.00 3.742 0.174 4.9 11/17/09 40,247,040.9 279.6 1,840.02,974.8 281 60.00 3.916 0.186 4.9 11/17/09 40,173,696.1 279.1 1,840.02,969.4 281 60.00 4.104 0.195 4.9 11/17/09 40,163,334.7 278.7 1,840.02,968.6 281 60.00 4.135 0.197 11/17/09 40,406,812.9 277.8 1,840.02,964.6 281 60.00 4.169 0.198

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 ST ST STC 15:00 ST ST ST 16:00 ST ST STC 17:00 SC 18:00 S 19:00 S 20:00 S 21:00 S 22:00 S 23:00 S 00:00 S 01:00 S 02:00 C S 03:00 S 04:00 SC 05:00 C SC 06:00 S 07:00 S 08:00 S 09:00 S 10:00 S 11:00 12:00 13:00 14:00 15:00 16:00 17:00 4.2 3.6 11/20/09 40,374,203.7 281.1 1,840.02,940.3 280 60.00 3.599 0.170 3.5 11/20/09 39,352,842.1 279.7 1,840.02,844.5 269 60.00 3.120 0.142 5.7 11/20/09 38,751,705.2 280.51,840.02,843.2 266 60.00 3.011 0.137 4.5 11/20/09 38,712,913.0 281.2 1,840.02,840.4 268 60.00 4.832 0.220 4.3 11/20/09 39,516,565.4 281.51,840.02,920.8 275 60.00 3.825 0.179 3.8 11/20/09 39,899,939.8 280.51,840.02,949.1 278 60.00 3.621 0.171 4.0 11/20/09 38,789,489.0 280.1 1,840.02,845.9 267 60.00 3.202 0.146 4.0 11/20/09 40,071,848.2 281.3 1,840.02,918.3 278 60.00 3.473 0.162 4.0 11/20/09 39,836,216.6 280.51,840.02,944.4 277 60.00 3.424 0.161 4.0 11/20/09 39,329,780.6 278.7 1,840.02,864.3 273 60.00 3.470 0.159 4.0 11/20/09 38,230,141.0 277.9 1,840.02,763.4 262 60.00 3.492 0.154 4.0 11/20/09 35,854,197.7 272.6 1,840.02,552.6 237 60.00 3.548 0.145 4.0 11/20/09 27,667,077.6 267.1 1,840.0 1,909.6 175 60.00 3.648 0.112 4.0 11/20/09 26,167,122.6 267.0 1,840.0 1,791.9 168 60.00 3.693 0.106 4.0 11/20/09 27,404,272.6 268.1 1,840.0 1,861.7 181 60.00 3.698 0.110 4.0 11/20/09 28,697,296.0 267.6 1,840.0 1,949.5 186 60.00 3.703 0.116 4.0 11/20/09 27,085,997.8 267.9 1,840.0 1,840.1 174 60.00 3.716 0.109 4.0 11/20/09 26,759,113.9 269.51,840.0 1,832.4 173 60.00 3.671 0.108 4.0 11/19/09 31,651,537.4 274.8 1,840.02,219.1 212 60.00 3.587 0.128 4.0 11/19/09 35,482,372.1 277.7 1,840.02,584.0 244 60.00 3.469 0.143 4.0 11/19/09 38,996,442.5 280.6 1,840.02,818.7 268 60.00 3.496 0.157 4.0 11/19/09 40,210,229.8 280.8 1,840.02,906.5 276 60.00 3.501 0.162 4.0 11/19/09 40,201,337.8 281.9 1,840.02,884.0 277 60.00 3.504 0.162 4.0 11/19/09 40,549,976.4 282.2 1,840.02,931.1 281 60.00 3.484 0.163 4.2 11/19/09 40,345,339.9 281.8 1,840.02,938.2 280 60.00 3.461 0.163 4.2 11/19/09 39,781,611.0 279.9 1,840.02,897.2 275 60.00 3.588 0.166 4.2 11/19/09 39,148,330.3 280.9 1,840.02,829.7 268 60.00 3.605 0.163 4.3 11/19/09 39,709,575.5 281.1 1,840.02,870.3 272 60.00 3.603 0.166 5.0 11/19/09 37,910,206.6 277.1 1,840.02,760.8 255 60.00 3.701 0.163 5.1 11/19/09 36,238,898.9 278.51,840.02,599.8 248 60.00 4.331 0.180 5.1 11/19/09 39,631,839.3 281.0 1,840.02,864.7 272 60.00 4.390 0.201 5.1 11/19/09 40,075,480.6 281.1 1,840.02,874.9 275 60.00 4.403 0.202 5.2 11/19/09 40,324,555.2 281.2 1,840.02,892.9 275 60.00 4.471 0.207 5.1 11/19/09 40,421,354.0 280.51,840.02,899.8 278 60.00 4.568 0.211 4.8 11/19/09 40,571,738.8 278.51,840.02,866.5 278 60.00 4.494 0.206 4.1 11/19/09 38,883,392.9 275.2 1,840.02,768.3 266 60.00 4.210 0.187 11/19/09 34,161,993.1 270.0 1,840.02,376.5 224 60.00 3.704 0.141

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 1.8 1.9 11/22/09 28,304,316.5 267.4 1,840.0 1,999.7 189 60.00 1.598 0.051 2.1 11/22/09 28,070,886.1 267.3 1,840.0 1,983.3 185 60.00 1.714 0.054 2.2 11/22/09 27,688,559.7 267.1 1,840.0 1,926.2 180 60.00 1.885 0.058 2.8 11/22/09 27,257,509.8 267.1 1,840.0 1,896.2 179 60.00 2.007 0.061 3.0 11/22/09 28,307,946.2 267.51,840.02,000.0 189 60.00 2.483 0.080 3.5 11/22/09 26,960,578.8 268.2 1,840.0 1,875.5 181 60.00 2.734 0.082 2.7 11/22/09 31,460,838.3 271.9 1,840.02,274.1 215 60.00 3.017 0.110 3.0 11/21/09 30,969,105.1 269.4 1,840.02,255.4 206 60.00 2.318 0.083 3.1 11/21/09 29,067,602.1 269.2 1,840.02,069.5 192 60.00 2.651 0.087 3.4 11/21/09 27,168,852.4 269.51,840.0 1,904.8 177 60.00 2.745 0.084 4.0 11/21/09 29,868,169.4 273.8 1,840.02,158.9 205 60.00 2.912 0.100 3.8 11/21/09 36,971,038.6 277.1 1,840.02,692.5 253 60.00 3.412 0.147 3.3 11/21/09 37,517,668.7 277.2 1,840.02,732.3 257 60.00 3.205 0.141 2.6 11/21/09 38,005,094.9 274.6 1,840.02,788.4 257 60.00 2.837 0.126 2.9 11/21/09 29,574,104.8 267.3 1,840.02,105.5 190 60.00 2.300 0.078 2.7 11/21/09 27,431,487.9 267.4 1,840.0 1,908.2 178 60.00 2.562 0.078 3.5 11/21/09 27,109,270.1 267.0 1,840.0 1,900.6 176 60.00 2.419 0.074 3.4 11/21/09 27,127,649.7 267.0 1,840.0 1,946.1 181 60.00 3.052 0.095 4.3 11/21/09 26,015,983.7 267.3 1,840.0 1,838.1 175 60.00 3.031 0.089 4.9 11/21/09 31,194,548.6 271.6 1,840.02,220.9 213 60.00 3.765 0.134 4.9 11/21/09 36,971,847.2 276.3 1,840.02,672.4 253 60.00 4.209 0.180 4.4 11/21/09 39,343,800.4 278.2 1,840.02,886.7 270 60.00 4.130 0.191 3.7 11/21/09 36,729,561.2 272.4 1,840.02,674.9 244 60.00 3.823 0.163 3.6 11/21/09 31,118,362.3 269.2 1,840.02,080.2 204 60.00 3.426 0.114 3.0 11/21/09 31,716,490.9 267.1 1,840.02,223.6 208 60.00 3.212 0.114 2.7 11/21/09 27,344,846.4 266.6 1,840.0 1,932.0 179 60.00 2.638 0.081 3.2 11/21/09 25,872,443.5 266.2 1,840.0 1,813.9 167 60.00 2.433 0.070 4.0 11/21/09 25,992,879.2 267.2 1,840.0 1,794.1 168 60.00 2.858 0.082 4.4 11/21/09 27,361,916.2 267.4 1,840.0 1,903.4 184 60.00 3.637 0.110 4.4 11/21/09 26,399,264.0 266.6 1,840.0 1,836.5 174 60.00 3.931 0.116 4.7 11/21/09 25,570,068.1 270.0 1,840.0 1,792.7 172 60.00 3.926 0.112 5.0 11/20/09 33,688,275.8 276.8 1,840.02,453.4 233 60.00 4.079 0.159 4.9 11/20/09 37,988,461.1 279.2 1,840.02,766.5 260 60.00 4.273 0.190 5.0 11/20/09 38,656,343.9 279.9 1,840.02,815.2 266 60.00 4.189 0.189 5.4 11/20/09 39,150,185.7 280.8 1,840.02,851.1 270 60.00 4.296 0.196 5.2 11/20/09 40,199,697.5 281.2 1,840.02,949.5 280 60.00 4.617 0.218 11/20/09 40,057,844.8 280.7 1,840.02,960.8 281 60.00 4.396 0.208

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 2.3 2.6 11/23/09 36,766,298.2 276.51,840.02,697.5 257 60.00 1.973 0.085 2.5 11/23/09 40,396,453.4 278.51,840.02,941.9 281 60.00 2.181 0.103 1.9 11/23/09 40,754,863.3 277.9 1,840.02,945.9 281 60.00 2.153 0.102 1.8 11/23/09 35,519,179.4 269.0 1,840.02,490.2 231 60.00 1.684 0.067 2.1 11/23/09 28,684,204.5 268.1 1,840.0 1,964.2 191 60.00 1.673 0.053 2.0 11/23/09 31,868,579.6 270.9 1,840.02,199.7 213 60.00 1.877 0.066 1.6 11/23/09 34,081,320.3 270.7 1,840.02,389.4 227 60.00 1.768 0.067 1.4 11/23/09 31,481,682.9 267.7 1,840.02,172.9 206 60.00 1.433 0.050 1.8 11/23/09 31,970,411.3 272.7 1,840.02,224.0 218 60.00 1.285 0.046 2.6 11/23/09 36,628,713.3 275.3 1,840.02,587.9 247 60.00 1.569 0.065 3.5 11/23/09 40,698,070.6 278.51,840.02,941.8 280 60.00 2.232 0.105 3.6 11/23/09 40,432,367.4 278.8 1,840.02,922.5 277 60.00 3.047 0.142 2.8 11/23/09 39,472,241.9 275.9 1,840.02,831.7 264 60.00 3.159 0.143 2.9 11/23/09 30,613,606.1 267.3 1,840.02,146.3 201 60.00 2.515 0.087 3.0 11/23/09 28,071,736.6 268.9 1,840.0 1,952.8 188 60.00 2.602 0.082 2.9 11/23/09 29,183,815.6 267.51,840.02,046.1 190 60.00 2.652 0.087 3.0 11/23/09 27,753,893.4 268.1 1,840.0 1,930.7 181 60.00 2.566 0.079 3.0 11/23/09 27,965,629.3 269.2 1,840.0 1,975.9 197 60.00 2.677 0.085 3.0 11/23/09 29,392,089.8 270.0 1,840.02,108.6 201 60.00 2.605 0.088 2.9 11/23/09 30,474,813.8 269.9 1,840.02,186.3 207 60.00 2.600 0.091 3.1 11/22/09 30,442,338.8 270.8 1,840.02,183.9 208 60.00 2.548 0.089 3.0 11/22/09 35,239,146.8 274.3 1,840.02,566.3 242 60.00 2.633 0.108 3.1 11/22/09 38,422,771.0 277.0 1,840.02,840.0 266 60.00 2.496 0.113 3.4 11/22/09 38,814,182.1 277.3 1,840.02,868.9 268 60.00 2.574 0.118 3.1 11/22/09 39,751,420.8 278.0 1,840.02,916.5 276 60.00 2.899 0.135 3.1 11/22/09 39,585,261.3 277.3 1,840.02,925.8 274 60.00 2.639 0.123 2.2 11/22/09 39,063,758.5 274.8 1,840.02,844.9 268 60.00 2.654 0.121 2.8 11/22/09 30,954,874.4 267.7 1,840.02,254.3 207 60.00 1.930 0.069 2.6 11/22/09 30,896,935.2 269.51,840.02,099.0 204 60.00 2.536 0.085 2.7 11/22/09 32,653,783.6 270.0 1,840.02,253.8 215 60.00 2.332 0.084 2.9 11/22/09 32,277,546.3 269.51,840.02,227.9 212 60.00 2.405 0.085 2.8 11/22/09 33,953,644.0 272.51,840.02,398.9 229 60.00 2.610 0.100 2.5 11/22/09 35,827,814.7 273.51,840.02,550.8 240 60.00 2.464 0.100 2.5 11/22/09 36,091,727.2 274.7 1,840.02,589.2 242 60.00 2.163 0.089 2.5 11/22/09 36,715,958.3 273.51,840.02,673.9 246 60.00 2.154 0.092 2.2 11/22/09 29,337,835.9 267.6 1,840.02,120.6 199 60.00 2.124 0.072 11/22/09 28,672,682.5 266.51,840.02,057.0 192 60.00 1.951 0.064

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 2.5 2.3 11/25/09 37,037,941.4 274.3 1,840.02,576.6 247 60.00 2.223 0.092 1.6 11/25/09 35,435,375.4 268.4 1,840.02,522.8 236 60.00 2.014 0.081 1.6 11/25/09 28,498,391.8 261.8 1,840.0 1,998.0 186 60.00 1.420 0.046 1.6 11/25/09 24,643,756.2 260.9 1,840.0 1,701.0 161 60.00 1.422 0.039 1.4 11/25/09 23,775,504.1 263.2 1,840.0 1,628.1 155 60.00 1.420 0.037 1.2 11/25/09 27,340,030.8 264.4 1,840.0 1,916.8 178 60.00 1.233 0.038 1.9 11/25/09 26,436,150.2 263.8 1,840.0 1,824.7 174 60.00 1.093 0.032 1.9 11/25/09 24,799,069.7 263.8 1,840.0 1,684.7 157 60.00 1.714 0.046 2.5 11/25/09 26,868,300.0 267.51,840.0 1,810.7 181 60.00 1.728 0.050 2.1 11/24/09 29,947,841.3 265.3 1,840.02,067.1 195 60.00 2.281 0.076 2.2 11/24/09 25,483,899.6 265.2 1,840.0 1,786.7 170 60.00 1.903 0.055 2.4 11/24/09 28,476,046.6 269.6 1,840.0 1,980.9 195 60.00 1.939 0.062 2.6 11/24/09 35,222,113.7 272.9 1,840.02,507.7 240 60.00 2.137 0.086 2.4 11/24/09 36,772,723.6 274.7 1,840.02,618.1 253 60.00 2.262 0.095 2.6 11/24/09 38,639,071.0 276.2 1,840.02,792.9 267 60.00 2.098 0.094 2.2 11/24/09 40,286,607.3 277.3 1,840.02,912.0 279 60.00 2.274 0.106 2.3 11/24/09 36,953,480.6 273.1 1,840.02,651.0 250 60.00 1.940 0.083 2.0 11/24/09 36,893,596.3 273.8 1,840.02,626.7 249 60.00 1.976 0.083 2.0 11/24/09 36,644,890.4 273.51,840.02,628.9 250 60.00 1.733 0.073 1.9 11/24/09 36,898,597.1 274.0 1,840.02,647.1 249 60.00 1.708 0.072 1.8 11/24/09 36,320,971.4 274.1 1,840.02,605.6 245 60.00 1.675 0.070 3.7 11/24/09 37,618,777.6 276.0 1,840.02,739.6 258 60.00 1.542 0.067 2.8 11/24/09 37,058,064.0 275.1 1,840.02,698.8 255 60.00 3.173 0.137 2.3 11/24/09 37,699,903.1 275.7 1,840.02,766.0 258 60.00 2.365 0.104 2.3 11/24/09 36,626,230.3 274.1 1,840.02,647.4 248 60.00 1.945 0.082 1.9 11/24/09 37,468,677.7 273.7 1,840.02,728.7 253 60.00 2.018 0.088 1.6 11/24/09 30,354,104.0 266.51,840.02,144.6 196 60.00 1.705 0.058 1.6 11/24/09 26,136,580.7 264.1 1,840.0 1,804.0 167 60.00 1.410 0.041 1.5 11/24/09 24,297,662.9 263.2 1,840.0 1,650.7 153 60.00 1.484 0.039 1.7 11/24/09 23,586,375.1 262.4 1,840.0 1,627.9 153 60.00 1.381 0.036 2.0 11/24/09 23,521,736.5 264.0 1,840.0 1,661.9 153 60.00 1.483 0.039 1.6 11/24/09 26,017,524.1 266.0 1,840.0 1,809.9 174 60.00 1.789 0.052 2.1 11/24/09 26,159,667.0 268.3 1,840.0 1,862.5 176 60.00 1.390 0.041 2.1 11/23/09 31,955,484.5 274.0 1,840.02,275.1 218 60.00 1.813 0.066 2.3 11/23/09 36,997,095.0 275.7 1,840.02,694.3 253 60.00 1.812 0.078 2.0 11/23/09 35,979,894.5 274.8 1,840.02,620.3 244 60.00 1.970 0.083 11/23/09 33,884,135.7 271.9 1,840.02,467.6 231 60.00 1.749 0.069

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 S I S S 16:00 S I S S 17:00 S I S S 18:00 19:00 20:00 21:00 1.4 1.9 11/26/09 30,110,998.9 268.2 1,840.02,111.0 199 60.00 1.231 0.042 2.6 11/26/09 30,297,574.1 271.3 1,840.02,140.6 204 60.00 1.714 0.059 2.7 11/26/09 35,984,928.0 275.0 1,840.02,562.0 245 60.00 2.236 0.092 2.5 11/26/09 37,485,429.1 275.3 1,840.02,689.1 257 60.00 2.387 0.103 2.3 11/26/09 38,913,000.0 49.51,840.02,791.6 258 60.00 2.178 0.097 2.0 11/26/09 38,913,000.0 0.0 1,840.02,770.4 238 60.00 2.009 0.089 1.3 11/26/09 32,711,000.0 67.0 1,840.02,240.0 209 60.00 1.779 0.064 1.4 11/26/09 29,960,926.8 265.6 1,840.02,051.7 194 60.00 1.194 0.039 2.3 11/26/09 28,825,026.7 265.51,840.0 1,958.2 189 60.00 1.325 0.041 2.6 11/26/09 29,382,244.6 269.4 1,840.0 1,948.2 192 60.00 2.123 0.066 2.5 11/26/09 35,027,162.1 273.0 1,840.02,417.6 232 60.00 2.330 0.090 2.7 11/26/09 36,700,239.9 274.2 1,840.02,573.0 245 60.00 2.190 0.090 2.4 11/26/09 34,286,310.4 269.6 1,840.02,441.0 228 60.00 2.332 0.091 1.9 11/26/09 29,356,139.0 265.9 1,840.02,042.2 196 60.00 2.166 0.071 1.2 11/26/09 27,494,287.5 265.51,840.0 1,882.7 182 60.00 1.737 0.052 1.3 11/26/09 27,816,850.8 263.9 1,840.0 1,935.1 180 60.00 1.118 0.035 1.1 11/26/09 24,818,306.8 263.2 1,840.0 1,686.0 159 60.00 1.231 0.033 2.1 11/26/09 25,415,686.9 263.2 1,840.0 1,740.4 163 60.00 1.002 0.028 2.3 11/26/09 23,586,695.3 262.9 1,840.0 1,602.4 153 60.00 1.912 0.049 2.6 11/26/09 24,272,354.6 264.1 1,840.0 1,675.3 154 60.00 2.033 0.055 3.6 11/26/09 25,718,628.6 269.51,840.0 1,719.3 173 60.00 2.381 0.066 2.8 11/26/09 34,228,051.3 273.1 1,840.02,418.3 231 60.00 3.162 0.122 2.6 11/25/09 29,347,256.7 267.0 1,840.02,041.5 193 60.00 2.507 0.082 2.9 11/25/09 27,378,187.5 268.51,840.0 1,874.8 184 60.00 2.370 0.071 3.6 11/25/09 31,557,406.6 272.8 1,840.02,178.1 214 60.00 2.624 0.091 3.4 11/25/09 38,796,495.5 276.3 1,840.02,719.9 265 60.00 3.202 0.139 3.4 11/25/09 39,475,349.8 277.1 1,840.02,789.0 270 60.00 2.989 0.133 3.2 11/25/09 39,468,000.8 277.1 1,840.02,788.5 269 60.00 3.002 0.133 3.2 11/25/09 40,120,444.4 277.6 1,840.02,834.6 275 60.00 2.855 0.130 2.3 11/25/09 40,958,579.8 278.2 1,840.02,893.8 278 60.00 2.813 0.130 2.3 11/25/09 38,610,743.6 273.6 1,840.02,728.0 260 60.00 2.027 0.089 1.9 11/25/09 35,106,497.8 272.2 1,840.02,442.2 236 60.00 2.104 0.082 2.0 11/25/09 34,896,238.0 271.4 1,840.02,427.5 234 60.00 1.708 0.066 1.9 11/25/09 37,197,690.3 272.9 1,840.02,587.7 251 60.00 1.794 0.074 2.0 11/25/09 35,855,277.8 271.51,840.02,474.8 240 60.00 1.698 0.067 1.8 11/25/09 36,623,779.9 273.51,840.02,567.7 247 60.00 1.774 0.073 11/25/09 36,746,272.2 272.2 1,840.02,576.2 246 60.00 1.595 0.066

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 1.6 1.3 11/28/09 36,145,302.7 274.3 1,840.02,553.7 245 60.00 1.417 0.058 1.0 11/28/09 37,179,959.0 271.51,840.02,647.1 247 60.00 1.151 0.049 1.3 11/28/09 30,463,748.1 263.3 1,840.02,168.9 198 60.00 0.857 0.030 0.9 11/28/09 24,527,723.3 261.7 1,840.0 1,653.0 160 60.00 1.182 0.031 0.8 11/28/09 27,088,078.8 263.0 1,840.0 1,884.4 179 60.00 0.843 0.025 0.6 11/28/09 25,256,004.2 261.6 1,840.0 1,715.8 162 60.00 0.697 0.019 0.9 11/28/09 24,730,032.2 261.4 1,840.0 1,653.1 156 60.00 0.596 0.016 0.8 11/28/09 24,022,956.4 261.0 1,840.0 1,592.8 152 60.00 0.830 0.021 0.9 11/28/09 24,140,205.9 262.0 1,840.0 1,574.3 155 60.00 0.805 0.020 1.2 11/28/09 24,256,083.9 262.2 1,840.0 1,634.6 154 60.00 0.846 0.022 1.7 11/28/09 23,923,962.3 262.8 1,840.0 1,586.3 149 60.00 1.172 0.030 1.8 11/27/09 25,546,248.7 265.7 1,840.0 1,707.7 167 60.00 1.548 0.042 1.4 11/27/09 30,271,231.6 267.51,840.02,122.3 205 60.00 1.557 0.053 1.4 11/27/09 29,552,397.5 267.51,840.02,071.9 196 60.00 1.243 0.041 1.8 11/27/09 28,924,810.7 268.51,840.02,027.9 193 60.00 1.264 0.041 2.0 11/27/09 31,679,679.5 273.4 1,840.02,203.8 214 60.00 1.595 0.056 1.8 11/27/09 39,611,142.6 276.8 1,840.02,863.2 271 60.00 1.740 0.080 1.2 11/27/09 39,226,586.1 275.7 1,840.02,856.7 270 60.00 1.561 0.071 1.5 11/27/09 34,673,104.5 270.7 1,840.02,487.4 232 60.00 1.056 0.042 1.7 11/27/09 33,531,311.9 271.7 1,840.02,369.0 225 60.00 1.308 0.050 2.1 11/27/09 34,728,792.1 273.8 1,840.02,453.7 235 60.00 1.511 0.060 2.5 11/27/09 36,543,977.9 274.0 1,840.02,621.6 248 60.00 1.848 0.078 2.4 11/27/09 37,583,378.2 275.3 1,840.02,716.6 257 60.00 2.191 0.095 1.9 11/27/09 38,369,679.3 274.51,840.02,794.3 261 60.00 2.079 0.093 1.9 11/27/09 38,499,477.7 275.2 1,840.02,782.8 264 60.00 1.626 0.073 1.9 11/27/09 37,393,432.8 275.0 1,840.02,723.2 256 60.00 1.603 0.070 1.9 11/27/09 37,555,666.5 273.7 1,840.02,714.6 253 60.00 1.622 0.070 2.4 11/27/09 34,494,735.2 272.0 1,840.02,399.7 228 60.00 1.741 0.067 2.6 11/27/09 34,478,960.3 271.9 1,840.02,436.0 232 60.00 2.125 0.083 1.8 11/27/09 34,632,560.5 270.51,840.02,446.9 232 60.00 2.307 0.090 2.2 11/27/09 29,437,628.4 265.7 1,840.02,063.9 196 60.00 1.634 0.054 2.3 11/27/09 29,046,705.1 268.4 1,840.02,004.9 194 60.00 2.013 0.065 2.1 11/27/09 31,533,206.0 269.6 1,840.02,193.6 215 60.00 2.037 0.071 2.1 11/27/09 30,858,997.3 270.3 1,840.02,163.5 206 60.00 1.886 0.065 2.0 11/27/09 33,288,573.8 268.1 1,840.02,370.0 222 60.00 1.861 0.071 1.6 11/26/09 28,101,594.5 266.51,840.0 1,970.2 190 60.00 1.763 0.055 11/26/09 32,360,707.7 269.51,840.02,286.4 218 60.00 1.439 0.053

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 2.6 2.8 11/29/09 32,223,507.3 271.0 1,840.02,311.7 217 60.00 2.224 0.082 3.2 11/29/09 34,072,298.7 273.2 1,840.02,407.3 230 60.00 2.507 0.096 2.9 11/29/09 37,250,478.6 274.2 1,840.02,652.0 253 60.00 2.835 0.120 3.0 11/29/09 37,730,323.7 274.4 1,840.02,706.7 258 60.00 2.569 0.111 3.1 11/29/09 39,388,364.1 275.9 1,840.02,804.3 269 60.00 2.670 0.119 3.2 11/29/09 38,953,536.7 276.3 1,840.02,773.4 267 60.00 2.702 0.120 3.0 11/29/09 40,190,105.8 277.4 1,840.02,905.0 277 60.00 2.730 0.127 2.6 11/29/09 37,831,602.9 273.9 1,840.02,734.6 260 60.00 2.591 0.113 2.8 11/29/09 37,166,762.0 274.9 1,840.02,686.5 255 60.00 2.231 0.096 2.6 11/29/09 39,890,229.3 276.4 1,840.02,861.7 273 60.00 2.434 0.111 2.7 11/29/09 38,403,101.1 274.6 1,840.02,755.0 262 60.00 2.249 0.099 2.6 11/29/09 38,524,024.2 274.0 1,840.02,763.7 265 60.00 2.310 0.102 2.6 11/29/09 39,144,313.3 275.1 1,840.02,808.2 269 60.00 2.247 0.101 2.3 11/29/09 38,906,102.0 274.8 1,840.02,812.2 266 60.00 2.236 0.101 2.3 11/29/09 36,110,317.7 271.8 1,840.02,610.1 246 60.00 2.020 0.085 1.8 11/29/09 33,203,530.9 267.3 1,840.02,382.0 223 60.00 2.050 0.078 1.7 11/29/09 26,670,018.9 260.7 1,840.0 1,869.8 173 60.00 1.626 0.049 1.5 11/29/09 23,425,193.7 260.9 1,840.0 1,629.6 154 60.00 1.551 0.040 1.4 11/29/09 23,359,122.8 261.2 1,840.0 1,625.0 151 60.00 1.314 0.034 1.5 11/29/09 23,379,168.4 260.6 1,840.0 1,601.0 149 60.00 1.289 0.033 1.6 11/29/09 24,059,722.7 259.7 1,840.0 1,556.1 149 60.00 1.455 0.036 1.4 11/29/09 23,371,524.7 259.51,840.0 1,498.9 149 60.00 1.549 0.037 1.4 11/29/09 23,754,313.1 261.4 1,840.0 1,536.3 151 60.00 1.313 0.032 1.1 11/29/09 25,209,116.4 263.4 1,840.0 1,712.6 166 60.00 1.250 0.034 1.3 11/28/09 26,449,186.4 262.51,840.0 1,782.4 168 60.00 1.046 0.030 1.5 11/28/09 25,065,843.0 264.0 1,840.0 1,689.2 163 60.00 1.209 0.033 1.4 11/28/09 28,215,413.7 265.8 1,840.0 1,962.8 187 60.00 1.362 0.043 1.7 11/28/09 27,563,997.0 265.51,840.0 1,887.5 179 60.00 1.300 0.039 2.5 11/28/09 29,044,979.2 270.0 1,840.02,004.7 196 60.00 1.496 0.048 2.5 11/28/09 36,013,782.2 273.6 1,840.02,544.5 246 60.00 2.238 0.091 2.0 11/28/09 37,498,554.5 272.51,840.02,649.4 253 60.00 2.195 0.093 1.9 11/28/09 33,288,440.7 268.6 1,840.02,333.8 219 60.00 1.785 0.067 1.8 11/28/09 30,093,737.9 267.4 1,840.02,093.5 197 60.00 1.663 0.056 2.2 11/28/09 28,854,905.2 266.9 1,840.0 1,991.6 189 60.00 1.667 0.053 1.9 11/28/09 30,300,872.2 267.4 1,840.02,058.5 203 60.00 2.020 0.067 1.6 11/28/09 31,666,120.5 268.1 1,840.02,220.1 215 60.00 1.695 0.060 11/28/09 33,583,902.0 270.8 1,840.02,372.8 226 60.00 1.396 0.053

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 3.3 3.6 12/01/09 39,660,121.0 276.4 1,840.02,888.3 277 60.00 2.813 0.130 2.4 12/01/09 39,816,183.6 276.0 1,840.02,878.0 279 60.00 3.101 0.143 3.1 12/01/09 39,149,338.8 275.8 1,840.02,829.8 274 60.00 2.095 0.095 3.3 12/01/09 40,188,633.5 276.8 1,840.02,905.0 280 60.00 2.681 0.124 3.1 12/01/09 39,986,883.2 276.51,840.02,890.4 281 60.00 2.830 0.131 2.9 12/01/09 40,109,789.7 275.7 1,840.02,899.3 281 60.00 2.655 0.123 1.9 12/01/09 37,409,623.4 268.8 1,840.02,602.4 251 60.00 2.582 0.107 1.8 12/01/09 31,228,106.9 265.2 1,840.02,155.4 207 60.00 1.706 0.059 1.8 12/01/09 26,273,612.5 263.8 1,840.0 1,784.9 173 60.00 1.676 0.048 1.6 12/01/09 27,274,370.4 264.6 1,840.0 1,823.2 178 60.00 1.632 0.048 2.0 12/01/09 26,724,164.6 264.9 1,840.0 1,786.4 180 60.00 1.487 0.043 2.0 12/01/09 28,041,237.6 265.4 1,840.0 1,905.0 186 60.00 1.793 0.055 2.3 12/01/09 28,221,937.0 267.6 1,840.0 1,886.6 186 60.00 1.819 0.055 2.9 11/30/09 33,306,875.2 272.1 1,840.02,317.0 225 60.00 2.070 0.077 2.4 11/30/09 39,528,966.6 276.3 1,840.02,814.3 273 60.00 2.514 0.113 2.4 11/30/09 39,773,525.9 276.7 1,840.02,853.4 275 60.00 2.115 0.097 2.6 11/30/09 39,880,445.9 276.51,840.02,861.0 274 60.00 2.119 0.097 3.4 11/30/09 38,653,828.8 277.2 1,840.02,752.0 266 60.00 2.302 0.101 3.8 11/30/09 40,616,354.9 278.4 1,840.02,869.6 277 60.00 3.016 0.139 3.0 11/30/09 39,832,131.2 275.1 1,840.02,857.5 275 60.00 3.265 0.149 2.6 11/30/09 33,196,358.4 270.1 1,840.02,363.4 224 60.00 2.626 0.099 3.0 11/30/09 33,404,669.6 273.8 1,840.02,378.3 227 60.00 2.296 0.087 3.1 11/30/09 38,791,984.4 277.8 1,840.02,804.0 268 60.00 2.581 0.116 2.8 11/30/09 40,381,367.0 277.1 1,840.02,940.8 280 60.00 2.614 0.123 3.1 11/30/09 37,894,555.8 275.6 1,840.02,739.1 258 60.00 2.457 0.108 2.9 11/30/09 39,384,787.6 277.9 1,840.02,846.9 272 60.00 2.661 0.121 3.3 11/30/09 39,439,982.1 275.7 1,840.02,829.4 269 60.00 2.525 0.114 3.5 11/30/09 38,523,783.3 276.51,840.02,763.7 266 60.00 2.831 0.125 2.8 11/30/09 40,059,369.8 274.1 1,840.02,873.8 276 60.00 3.060 0.140 2.2 11/30/09 34,758,991.9 268.2 1,840.02,455.8 231 60.00 2.465 0.097 2.1 11/30/09 28,349,151.9 265.0 1,840.0 1,956.7 186 60.00 2.006 0.063 2.5 11/30/09 27,476,026.7 263.3 1,840.0 1,896.4 176 60.00 1.923 0.058 2.6 11/30/09 25,245,654.7 264.1 1,840.0 1,728.8 162 60.00 2.292 0.063 2.7 11/30/09 28,053,438.6 266.8 1,840.0 1,905.8 186 60.00 2.350 0.072 2.5 11/30/09 29,978,382.0 267.6 1,840.02,036.5 198 60.00 2.501 0.082 2.4 11/30/09 29,225,655.9 267.1 1,840.02,049.0 194 60.00 2.218 0.073 11/30/09 28,911,721.9 269.1 1,840.02,042.7 195 60.00 2.130 0.070

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 S S S 11:00 S S S 12:00 S S S 13:00 S S S 14:00 S S S 15:00 C 16:00 C 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 0.6 0.6 12/03/09 27,693,695.3 264.0 1,840.0 1,941.6 184 60.00 0.529 0.016 1.0 12/03/09 26,963,893.9 262.9 1,840.0 1,875.8 175 60.00 0.531 0.016 1.3 12/02/09 26,318,437.5 267.51,840.0 1,802.2 178 60.00 0.872 0.025 2.2 12/02/09 33,037,037.1 269.8 1,840.02,316.2 225 60.00 1.167 0.043 2.0 12/02/09 35,799,887.6 273.9 1,840.02,509.9 247 60.00 1.977 0.079 1.9 12/02/09 39,365,707.6 275.4 1,840.02,824.1 272 60.00 1.761 0.079 2.1 12/02/09 40,355,988.4 276.3 1,840.02,873.2 276 60.00 1.645 0.075 2.6 12/02/09 40,303,441.8 276.2 1,840.02,869.4 277 60.00 1.845 0.084 2.8 12/02/09 40,353,981.1 276.6 1,840.02,895.0 277 60.00 2.226 0.103 1.6 12/02/09 39,639,491.4 275.7 1,840.02,843.7 273 60.00 2.446 0.111 1.8 12/02/09 39,339,378.7 275.4 1,840.02,822.1 270 60.00 1.366 0.061 1.8 12/02/09 40,046,917.1 275.7 1,840.02,829.4 275 60.00 1.617 0.073 1.8 12/02/09 39,765,130.1 274.8 1,840.02,809.5 274 60.00 1.615 0.072 1.8 12/02/09 39,718,097.0 274.6 1,840.02,827.7 275 60.00 1.605 0.072 1.8 12/02/09 40,348,766.6 275.8 1,840.02,828.8 277 60.00 1.627 0.074 2.1 12/02/09 40,368,814.4 276.51,840.02,874.1 278 60.00 1.602 0.074 2.4 12/02/09 40,255,328.1 276.6 1,840.02,887.9 276 60.00 1.820 0.084 2.2 12/02/09 40,319,921.0 276.1 1,840.02,892.5 277 60.00 2.065 0.096 1.7 12/02/09 39,919,673.1 275.3 1,840.02,885.5 276 60.00 1.866 0.086 1.7 12/02/09 37,969,566.0 272.0 1,840.02,744.6 261 60.00 1.496 0.066 1.9 12/02/09 35,304,120.0 270.51,840.02,475.1 236 60.00 1.520 0.060 1.5 12/02/09 33,834,794.6 269.9 1,840.02,353.7 223 60.00 1.665 0.063 1.6 12/02/09 30,877,771.8 266.8 1,840.02,131.3 201 60.00 1.323 0.045 1.7 12/02/09 28,514,371.1 264.9 1,840.0 1,859.6 184 60.00 1.542 0.046 1.8 12/02/09 27,616,017.2 268.2 1,840.0 1,876.1 187 60.00 1.578 0.048 2.2 12/02/09 34,555,775.4 271.3 1,840.02,441.5 236 60.00 1.568 0.061 2.7 12/01/09 35,333,726.2 274.2 1,840.02,477.2 243 60.00 1.944 0.077 2.3 12/01/09 39,906,752.6 276.0 1,840.02,862.9 275 60.00 2.321 0.106 2.0 12/01/09 40,144,050.9 276.3 1,840.02,879.9 275 60.00 2.005 0.092 2.0 12/01/09 39,942,658.3 276.3 1,840.02,843.8 275 60.00 1.755 0.080 2.0 12/01/09 39,867,088.2 276.7 1,840.02,860.0 274 60.00 1.706 0.078 1.7 12/01/09 40,030,182.1 276.3 1,840.02,893.5 274 60.00 1.698 0.078 1.4 12/01/09 39,967,114.8 277.3 1,840.02,910.6 279 60.00 1.447 0.068 1.8 12/01/09 38,644,464.5 275.51,840.02,814.3 268 60.00 1.155 0.052 2.1 12/01/09 37,406,397.0 276.8 1,840.02,703.8 258 60.00 1.576 0.068 2.6 12/01/09 39,092,901.1 276.6 1,840.02,847.0 273 60.00 1.797 0.082 12/01/09 39,333,247.6 276.3 1,840.02,843.1 275 60.00 2.274 0.103

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

02:00 C 03:00 04:00 ST ST STC 05:00 C ST ST STC 06:00 ST ST ST 07:00 ST ST ST 08:00 ST ST ST 09:00 ST ST ST 10:00 ST ST ST 11:00 ST ST ST 12:00 ST ST ST 13:00 ST ST ST 14:00 ST ST ST 15:00 ST ST ST 16:00 ST ST ST 17:00 MC 18:00 19:00 C 20:00 C 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 C 07:00 C 08:00 C 09:00 C 10:00 M 11:00 S S SC 12:00 C 13:00 14:00 2.8 2.5 12/04/09 39,018,515.4 274.4 1,840.02,799.2 266 60.00 2.428 0.109 2.6 12/04/09 39,169,854.2 274.9 1,840.02,810.0 267 60.00 2.214 0.100 2.4 12/04/09 39,180,648.2 275.3 1,840.02,853.4 271 60.00 2.256 0.103 2.2 12/04/09 39,696,933.1 276.0 1,840.02,869.4 273 60.00 2.102 0.096 2.5 12/04/09 39,731,330.6 276.7 1,840.02,871.9 274 60.00 1.936 0.089 2.7 12/04/09 40,135,145.3 277.6 1,840.02,944.7 277 60.00 2.107 0.099 2.5 12/04/09 40,149,636.5 276.2 1,840.02,967.6 278 60.00 2.292 0.109 2.2 12/04/09 39,374,624.4 276.7 1,840.02,910.3 274 60.00 2.087 0.097 2.0 12/04/09 39,541,968.5 274.3 1,840.02,879.7 271 60.00 1.850 0.085 1.9 12/04/09 34,191,744.6 267.9 1,840.02,434.3 224 60.00 1.765 0.069 1.8 12/04/09 27,591,787.4 263.6 1,840.0 1,934.4 179 60.00 1.652 0.051 1.7 12/04/09 27,526,877.0 265.7 1,840.0 1,914.9 184 60.00 1.665 0.051 2.1 12/04/09 28,637,636.3 266.1 1,840.0 1,930.0 184 60.00 1.561 0.048 3.5 12/04/09 29,244,954.3 269.7 1,840.02,018.5 194 60.00 1.891 0.061 3.7 12/04/09 34,574,758.5 272.3 1,840.02,461.6 233 60.00 3.077 0.121 4.0 12/03/09 32,241,755.4 269.6 1,840.02,278.0 217 60.00 3.254 0.119 4.1 12/03/09 34,803,813.7 273.8 1,840.02,440.1 237 60.00 3.521 0.138 3.9 12/03/09 38,859,235.7 276.8 1,840.02,787.7 267 60.00 3.581 0.160 3.1 12/03/09 39,899,541.3 276.9 1,840.02,862.4 275 60.00 3.387 0.155 2.8 12/03/09 40,226,389.9 277.0 1,840.02,885.8 278 60.00 2.720 0.125 2.0 12/03/09 40,060,376.5 276.8 1,840.02,895.6 277 60.00 2.396 0.111 1.1 12/03/09 40,281,899.0 277.9 1,840.02,911.7 277 60.00 1.717 0.080 1.1 12/03/09 39,863,899.8 275.7 1,840.02,838.1 271 60.00 0.959 0.044 1.1 12/03/09 39,303,942.3 275.6 1,840.02,776.9 266 60.00 0.966 0.043 1.1 12/03/09 39,816,529.7 276.3 1,840.02,834.8 271 60.00 0.963 0.044 1.1 12/03/09 39,945,357.0 275.7 1,840.02,843.9 274 60.00 0.960 0.044 1.1 12/03/09 39,388,199.9 275.0 1,840.02,825.7 271 60.00 0.958 0.043 1.1 12/03/09 38,956,699.3 276.4 1,840.02,794.7 267 60.00 0.955 0.043 1.1 12/03/09 39,717,098.8 277.0 1,840.02,849.3 273 60.00 0.952 0.043 1.1 12/03/09 39,729,132.6 276.8 1,840.02,850.1 273 60.00 0.957 0.044 1.1 12/03/09 39,841,418.9 276.2 1,840.02,858.2 274 60.00 0.956 0.044 1.1 12/03/09 38,622,600.8 272.6 1,840.02,749.8 263 60.00 0.964 0.042 1.1 12/03/09 32,625,511.2 267.0 1,840.02,269.6 218 60.00 0.985 0.036 1.1 12/03/09 30,597,593.4 264.6 1,840.02,128.6 199 60.00 0.984 0.034 0.2 12/03/09 26,387,654.6 264.2 1,840.0 1,778.3 169 60.00 1.016 0.029 0.2 12/03/09 29,408,915.7 267.3 1,840.02,029.9 194 60.00 0.180 0.006 12/03/09 29,561,404.9 265.7 1,840.02,040.4 195 60.00 0.209 0.007

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

15:00 S S S 16:00 S S S 17:00 18:00 C 19:00 ST ST STC 20:00 ST ST ST 21:00 ST ST ST 22:00 ST ST ST 23:00 ST ST STC 00:00 ST ST STC 01:00 ST ST STC 02:00 C C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 4.1 4.4 12/06/09 24,534,244.6 267.6 1,840.0 1,613.4 161 60.00 3.833 0.099 3.7 12/06/09 30,290,618.3 268.7 1,840.02,024.9 201 60.00 4.089 0.132 2.7 12/06/09 28,219,244.1 267.4 1,840.0 1,947.7 188 60.00 3.396 0.105 2.9 12/06/09 26,736,441.1 266.8 1,840.0 1,874.4 178 60.00 2.429 0.073 3.3 12/05/09 29,752,259.4 273.4 1,840.02,085.9 205 60.00 2.597 0.087 3.0 12/05/09 39,596,471.8 277.7 1,840.02,840.6 271 60.00 2.869 0.130 3.0 12/05/09 39,536,669.0 277.9 1,840.02,793.4 271 60.00 2.614 0.117 2.7 12/05/09 40,028,484.8 278.8 1,840.02,871.6 277 60.00 2.589 0.119 2.3 12/05/09 39,462,856.5 278.3 1,840.02,938.3 277 60.00 2.290 0.107 3.2 12/05/09 39,784,925.9 277.2 1,840.02,832.5 274 60.00 2.031 0.092 2.9 12/05/09 39,242,798.0 275.3 1,840.02,815.3 268 60.00 2.820 0.127 2.7 12/05/09 33,594,381.8 268.1 1,840.02,337.0 220 60.00 2.585 0.097 3.0 12/05/09 30,280,132.0 269.51,840.02,090.0 203 60.00 2.405 0.080 2.5 12/05/09 36,458,006.2 271.7 1,840.02,575.8 249 60.00 2.636 0.109 2.8 12/05/09 34,603,790.5 272.7 1,840.02,426.0 234 60.00 2.226 0.086 2.7 12/05/09 39,886,841.5 275.2 1,840.02,861.5 272 60.00 2.407 0.110 2.7 12/05/09 39,440,318.8 274.9 1,840.02,808.0 270 60.00 2.371 0.107 2.6 12/05/09 39,474,876.5 275.1 1,840.02,831.9 273 60.00 2.359 0.107 2.9 12/05/09 39,441,687.6 274.3 1,840.02,829.5 270 60.00 2.272 0.103 2.3 12/05/09 40,010,204.5 273.8 1,840.02,848.5 272 60.00 2.510 0.114 2.0 12/05/09 36,907,152.9 269.3 1,840.02,647.7 247 60.00 1.973 0.084 2.2 12/05/09 29,405,799.6 263.4 1,840.02,045.6 191 60.00 1.819 0.059 2.3 12/05/09 27,786,986.3 265.3 1,840.0 1,887.7 184 60.00 2.012 0.061 2.4 12/05/09 30,012,919.0 266.7 1,840.02,071.5 198 60.00 2.107 0.070 2.4 12/05/09 28,681,482.3 265.9 1,840.02,042.0 192 60.00 2.108 0.069 2.5 12/05/09 29,959,914.4 271.4 1,840.02,149.3 207 60.00 2.058 0.071 2.5 12/05/09 38,573,936.7 275.1 1,840.02,788.2 264 60.00 2.171 0.097 2.5 12/05/09 39,258,107.0 275.51,840.02,837.7 269 60.00 2.172 0.099 2.5 12/04/09 40,321,786.0 276.7 1,840.02,936.5 278 60.00 2.160 0.101 2.5 12/04/09 39,566,640.3 275.8 1,840.02,903.0 273 60.00 2.148 0.099 2.5 12/04/09 39,766,103.3 275.3 1,840.02,896.0 275 60.00 2.165 0.100 2.5 12/04/09 39,945,459.0 275.51,840.02,909.0 275 60.00 2.165 0.100 2.7 12/04/09 40,034,032.2 275.7 1,840.02,893.8 274 60.00 2.176 0.101 2.7 12/04/09 40,385,484.2 276.1 1,840.02,919.1 277 60.00 2.311 0.108 2.8 12/04/09 40,211,744.1 276.0 1,840.02,928.5 278 60.00 2.335 0.109 2.8 12/04/09 39,696,430.5 274.9 1,840.02,890.9 273 60.00 2.365 0.109 12/04/09 39,820,096.3 275.2 1,840.02,878.3 273 60.00 2.377 0.110

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 2.9 3.2 12/07/09 39,979,970.5 277.1 1,840.02,868.1 273 60.00 2.542 0.117 3.5 12/07/09 39,946,020.3 277.51,840.02,887.4 273 60.00 2.800 0.129 3.8 12/07/09 39,637,068.2 277.6 1,840.02,843.5 270 60.00 3.031 0.137 4.3 12/07/09 40,167,790.4 279.4 1,840.02,881.6 274 60.00 3.272 0.151 4.2 12/07/09 40,082,391.8 279.3 1,840.02,875.4 274 60.00 3.720 0.171 4.2 12/07/09 40,132,966.1 279.2 1,840.02,879.1 274 60.00 3.707 0.170 4.3 12/07/09 39,859,494.5 279.2 1,840.02,881.1 274 60.00 3.619 0.167 4.3 12/07/09 39,945,700.0 278.6 1,840.02,909.1 274 60.00 3.659 0.170 4.4 12/07/09 40,054,442.2 278.7 1,840.02,917.0 275 60.00 3.703 0.173 4.4 12/07/09 39,782,008.8 278.51,840.02,875.5 272 60.00 3.761 0.173 3.7 12/07/09 39,085,004.8 275.8 1,840.02,803.9 263 60.00 3.859 0.173 2.6 12/07/09 32,259,243.8 268.7 1,840.02,296.7 214 60.00 3.214 0.118 3.0 12/07/09 28,785,720.4 267.51,840.02,002.5 191 60.00 2.296 0.074 3.2 12/07/09 28,774,947.1 267.2 1,840.0 1,986.1 189 60.00 2.687 0.085 3.6 12/07/09 29,240,612.1 269.2 1,840.0 1,954.7 189 60.00 2.960 0.092 3.6 12/07/09 30,681,779.2 271.1 1,840.02,117.7 204 60.00 3.231 0.109 4.0 12/07/09 31,018,384.2 272.3 1,840.02,191.5 209 60.00 3.156 0.111 4.4 12/06/09 33,213,865.0 275.3 1,840.02,382.7 225 60.00 3.464 0.132 4.5 12/06/09 37,006,836.5 278.0 1,840.02,614.6 250 60.00 3.905 0.164 4.5 12/06/09 38,995,435.3 279.8 1,840.02,797.5 266 60.00 3.874 0.173 4.6 12/06/09 40,445,882.9 280.1 1,840.02,923.5 277 60.00 3.849 0.180 4.5 12/06/09 40,500,702.0 279.6 1,840.02,927.5 277 60.00 3.987 0.186 4.4 12/06/09 40,433,346.7 279.0 1,840.02,922.6 278 60.00 3.873 0.181 4.6 12/06/09 40,487,799.8 278.9 1,840.02,926.6 277 60.00 3.794 0.178 4.2 12/06/09 39,339,185.7 276.2 1,840.02,800.8 264 60.00 4.026 0.180 4.0 12/06/09 38,134,133.1 275.0 1,840.02,673.5 254 60.00 3.700 0.158 4.2 12/06/09 38,114,331.9 277.51,840.02,713.6 258 60.00 3.527 0.153 4.4 12/06/09 39,303,251.0 278.7 1,840.02,840.9 268 60.00 3.614 0.164 4.2 12/06/09 40,024,078.1 280.1 1,840.02,893.0 274 60.00 3.751 0.174 5.3 12/06/09 40,527,300.3 280.51,840.02,929.4 277 60.00 3.588 0.168 5.5 12/06/09 39,387,261.2 281.2 1,840.02,825.6 268 60.00 4.573 0.207 5.5 12/06/09 39,168,564.8 279.3 1,840.02,810.0 266 60.00 4.792 0.215 5.3 12/06/09 38,798,974.9 277.51,840.02,762.3 263 60.00 4.821 0.214 4.6 12/06/09 37,645,227.9 275.51,840.02,659.7 254 60.00 4.691 0.199 3.1 12/06/09 35,725,163.4 271.0 1,840.02,524.0 238 60.00 4.082 0.165 2.7 12/06/09 28,715,982.5 265.51,840.02,060.1 193 60.00 2.680 0.088 12/06/09 26,070,446.6 265.1 1,840.0 1,799.4 170 60.00 2.434 0.070

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 ST ST STC 13:00 ST ST ST 14:00 ST ST ST 15:00 ST ST ST 16:00 ST ST ST 17:00 ST ST ST 18:00 ST ST ST 19:00 ST ST ST 20:00 ST ST ST 21:00 ST ST ST 22:00 ST ST ST 23:00 ST ST ST 00:00 ST ST ST 01:00 ST ST ST 02:00 C ST ST ST 03:00 ST ST ST 04:00 ST ST STC 05:00 C C 4.9 3.9 12/09/09 33,254,930.1 269.6 1,840.02,313.4 226 60.00 4.338 0.161 3.9 12/09/09 33,425,450.1 270.51,840.02,307.1 224 60.00 3.492 0.128 3.9 12/09/09 30,490,048.8 264.51,840.02,054.8 194 60.00 3.555 0.117 3.9 12/09/09 26,373,648.2 264.4 1,840.0 1,705.7 169 60.00 3.714 0.101 3.9 12/09/09 28,150,831.9 266.0 1,840.0 1,897.1 185 60.00 3.576 0.108 3.9 12/09/09 33,018,410.3 267.3 1,840.02,279.0 220 60.00 3.494 0.127 3.9 12/08/09 29,032,805.1 263.4 1,840.0 1,988.1 191 60.00 3.505 0.112 3.9 12/08/09 27,585,726.7 266.51,840.0 1,874.0 184 60.00 3.533 0.106 3.9 12/08/09 33,566,881.5 271.7 1,840.02,316.9 228 60.00 3.487 0.129 3.9 12/08/09 36,511,751.2 274.2 1,840.02,579.7 248 60.00 3.400 0.140 3.9 12/08/09 39,744,008.5 275.8 1,840.02,851.2 272 60.00 3.351 0.153 3.9 12/08/09 38,831,057.2 272.1 1,840.02,764.6 263 60.00 3.364 0.149 3.9 12/08/09 32,821,153.7 264.3 1,840.02,318.9 217 60.00 3.402 0.126 3.9 12/08/09 25,830,860.3 261.8 1,840.0 1,768.9 167 60.00 3.515 0.099 3.9 12/08/09 23,691,995.9 263.51,840.0 1,596.6 152 60.00 3.566 0.091 3.9 12/08/09 26,817,418.1 265.0 1,840.0 1,821.8 173 60.00 3.551 0.103 3.9 12/08/09 30,520,476.1 268.3 1,840.02,106.5 203 60.00 3.491 0.117 2.8 12/08/09 32,564,257.5 270.4 1,840.02,283.0 221 60.00 3.440 0.125 2.9 12/08/09 37,537,324.9 274.7 1,840.02,713.3 257 60.00 2.465 0.107 2.8 12/08/09 38,568,381.3 275.3 1,840.02,829.7 265 60.00 2.491 0.113 2.7 12/08/09 36,079,049.1 273.9 1,840.02,607.9 244 60.00 2.432 0.101 2.0 12/08/09 38,867,386.0 273.6 1,840.02,830.5 265 60.00 2.361 0.106 2.1 12/08/09 32,313,776.3 266.8 1,840.02,335.7 217 60.00 1.744 0.065 2.4 12/08/09 29,111,127.2 267.51,840.02,009.3 197 60.00 1.888 0.061 2.0 12/08/09 33,910,330.0 269.9 1,840.02,395.8 231 60.00 2.102 0.080 2.4 12/08/09 34,534,630.3 270.9 1,840.02,458.7 235 60.00 1.787 0.070 2.8 12/08/09 33,389,776.0 270.3 1,840.02,395.4 228 60.00 2.077 0.080 3.0 12/08/09 32,553,421.1 271.0 1,840.02,299.9 220 60.00 2.474 0.091 3.7 12/08/09 34,201,512.9 273.0 1,840.02,435.0 233 60.00 2.640 0.103 3.2 12/08/09 35,725,754.1 274.7 1,840.02,621.2 247 60.00 3.170 0.133 3.5 12/07/09 35,628,613.3 271.3 1,840.02,556.0 242 60.00 2.807 0.115 3.2 12/07/09 38,737,787.0 275.51,840.02,758.0 264 60.00 3.049 0.134 3.2 12/07/09 40,878,049.8 276.9 1,840.02,932.6 277 60.00 2.823 0.132 3.3 12/07/09 40,381,102.3 277.0 1,840.02,918.8 277 60.00 2.739 0.128 3.4 12/07/09 40,510,367.9 277.2 1,840.02,928.2 278 60.00 2.809 0.132 3.6 12/07/09 40,661,591.4 277.1 1,840.02,917.1 277 60.00 2.977 0.139 12/07/09 39,830,938.4 276.2 1,840.02,879.1 274 60.00 3.139 0.145

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 M 14:00 M 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C C 03:00 C 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 3.5 3.6 12/10/09 40,395,319.5 280.0 1,840.02,897.9 282 60.00 3.020 0.140 3.5 12/10/09 40,132,295.0 279.6 1,840.02,900.8 282 60.00 3.086 0.143 3.1 12/10/09 39,748,488.0 277.8 1,840.02,873.1 279 60.00 3.015 0.139 2.6 12/10/09 38,597,885.5 275.9 1,840.02,769.0 269 60.00 2.709 0.120 2.8 12/10/09 38,413,523.6 275.3 1,840.02,734.9 267 60.00 2.257 0.099 2.8 12/10/09 39,679,931.9 278.0 1,840.02,846.6 276 60.00 2.455 0.112 2.7 12/10/09 39,562,024.9 277.2 1,840.02,859.6 275 60.00 2.418 0.110 3.6 12/10/09 38,360,598.6 277.1 1,840.02,752.0 264 60.00 2.374 0.104 4.0 12/10/09 40,411,276.8 280.7 1,840.02,921.0 281 60.00 3.143 0.147 3.7 12/10/09 40,382,155.6 279.3 1,840.02,918.9 281 60.00 3.432 0.160 3.2 12/10/09 40,416,590.8 278.2 1,840.02,921.4 282 60.00 3.172 0.148 2.7 12/10/09 40,079,024.6 276.51,840.02,897.0 278 60.00 2.790 0.129 2.3 12/10/09 40,086,390.6 275.51,840.02,875.7 276 60.00 2.385 0.110 2.3 12/10/09 38,344,565.9 273.1 1,840.02,709.2 259 60.00 2.079 0.090 2.8 12/10/09 34,438,660.9 270.8 1,840.02,433.2 231 60.00 1.999 0.078 2.7 12/10/09 35,697,076.9 273.0 1,840.02,463.9 243 60.00 2.550 0.101 2.7 12/10/09 38,862,312.4 274.7 1,840.02,682.3 264 60.00 2.416 0.104 2.5 12/10/09 36,268,462.5 271.8 1,840.02,523.0 245 60.00 2.409 0.097 2.3 12/10/09 35,861,812.8 271.6 1,840.02,475.3 242 60.00 2.282 0.090 2.4 12/09/09 36,461,811.8 274.51,840.02,536.5 248 60.00 2.063 0.083 2.5 12/09/09 39,828,419.2 276.7 1,840.02,813.9 272 60.00 2.117 0.095 2.8 12/09/09 39,202,479.5 277.0 1,840.02,748.4 267 60.00 2.225 0.098 3.0 12/09/09 40,046,849.1 277.7 1,840.02,829.4 275 60.00 2.454 0.111 3.2 12/09/09 40,079,680.1 276.8 1,840.02,810.0 274 60.00 2.632 0.118 3.4 12/09/09 40,387,644.9 277.4 1,840.02,831.6 275 60.00 2.806 0.127 3.3 12/09/09 40,209,094.9 277.4 1,840.02,819.0 275 60.00 3.015 0.136 3.7 12/09/09 39,593,848.7 276.8 1,840.02,775.9 270 60.00 2.922 0.129 3.0 12/09/09 39,321,643.9 275.51,840.02,756.8 268 60.00 3.304 0.145 3.4 12/09/09 37,824,034.9 274.7 1,840.02,610.7 256 60.00 2.716 0.114 3.4 12/09/09 39,465,257.4 275.4 1,840.02,723.9 269 60.00 3.070 0.134 3.6 12/09/09 39,515,507.2 276.2 1,840.02,727.5 270 60.00 3.029 0.132 3.4 12/09/09 40,210,413.0 276.6 1,840.02,797.2 273 60.00 3.198 0.143 3.8 12/09/09 39,966,526.5 277.2 1,840.02,736.9 268 60.00 3.105 0.136 4.0 12/09/09 40,362,020.2 277.6 1,840.02,807.8 274 60.00 3.408 0.153 4.7 12/09/09 40,403,147.1 277.8 1,840.02,810.6 276 60.00 3.587 0.162 5.1 12/09/09 39,534,540.2 275.7 1,840.02,750.3 269 60.00 4.204 0.184 12/09/09 33,212,529.0 270.4 1,840.02,292.4 224 60.00 4.646 0.170

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 1.5 1.0 12/12/09 35,580,750.2 270.3 1,840.02,591.2 242 60.00 1.320 0.055 0.5 12/12/09 29,842,050.8 267.2 1,840.02,140.8 205 60.00 0.884 0.030 0.8 12/12/09 28,477,379.7 262.2 1,840.02,027.4 187 60.00 0.473 0.015 0.8 12/12/09 22,927,412.6 260.8 1,840.0 1,594.9 152 60.00 0.726 0.019 1.1 12/12/09 23,764,794.1 261.51,840.0 1,575.7 151 60.00 0.771 0.019 1.4 12/12/09 23,447,384.8 263.9 1,840.0 1,516.4 149 60.00 1.023 0.025 1.5 12/12/09 28,217,288.4 266.6 1,840.0 1,932.3 185 60.00 1.297 0.040 1.7 12/12/09 27,202,582.6 265.3 1,840.0 1,877.6 180 60.00 1.375 0.041 2.5 12/11/09 27,648,945.6 268.7 1,840.0 1,923.4 187 60.00 1.503 0.046 2.2 12/11/09 36,345,304.5 274.9 1,840.02,567.9 250 60.00 2.217 0.091 2.3 12/11/09 39,995,721.6 276.6 1,840.02,869.3 274 60.00 1.926 0.088 2.5 12/11/09 40,009,673.3 277.2 1,840.02,870.3 275 60.00 1.966 0.090 2.4 12/11/09 39,583,483.7 277.2 1,840.02,882.7 272 60.00 2.165 0.100 2.4 12/11/09 39,958,712.9 277.0 1,840.02,866.6 274 60.00 2.082 0.096 2.1 12/11/09 40,208,369.1 276.9 1,840.02,906.3 279 60.00 2.109 0.098 2.1 12/11/09 40,115,636.0 277.3 1,840.02,899.7 277 60.00 1.801 0.084 2.3 12/11/09 40,198,214.9 277.1 1,840.02,861.9 275 60.00 1.801 0.083 2.8 12/11/09 40,436,703.4 277.4 1,840.02,900.9 277 60.00 1.991 0.092 2.0 12/11/09 40,189,915.4 277.4 1,840.02,905.0 278 60.00 2.439 0.113 2.1 12/11/09 40,148,997.9 277.51,840.02,923.9 280 60.00 1.729 0.081 2.8 12/11/09 40,063,913.3 277.2 1,840.02,895.9 277 60.00 1.858 0.086 3.2 12/11/09 40,504,904.3 277.4 1,840.02,883.8 280 60.00 2.423 0.112 3.5 12/11/09 40,434,349.2 278.1 1,840.02,900.7 279 60.00 2.795 0.130 3.5 12/11/09 40,925,222.4 278.8 1,840.02,935.9 280 60.00 3.008 0.141 2.4 12/11/09 40,303,139.4 277.2 1,840.02,935.1 279 60.00 3.027 0.142 1.5 12/11/09 36,411,748.6 269.2 1,840.02,632.0 246 60.00 2.074 0.087 2.0 12/11/09 31,080,902.6 268.7 1,840.02,195.9 214 60.00 1.357 0.048 1.4 12/11/09 34,250,051.1 269.3 1,840.02,457.1 228 60.00 1.743 0.068 1.7 12/11/09 27,824,994.8 265.0 1,840.0 1,905.4 181 60.00 1.313 0.040 2.2 12/11/09 29,779,532.9 274.2 1,840.02,055.5 209 60.00 1.529 0.050 2.2 12/11/09 38,404,747.6 278.4 1,840.02,796.9 269 60.00 1.919 0.086 2.8 12/11/09 39,912,798.2 278.6 1,840.02,928.4 279 60.00 1.914 0.089 2.4 12/10/09 39,727,136.5 277.4 1,840.02,871.6 277 60.00 2.411 0.111 2.6 12/10/09 40,264,502.0 278.1 1,840.02,910.5 280 60.00 2.080 0.097 2.6 12/10/09 40,853,594.6 278.2 1,840.02,908.6 282 60.00 2.231 0.104 2.8 12/10/09 40,876,696.8 278.1 1,840.02,910.3 282 60.00 2.236 0.104 12/10/09 40,679,790.2 280.0 1,840.02,896.2 281 60.00 2.443 0.113

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 1.0 1.1 12/13/09 39,473,455.6 279.3 1,840.02,874.7 273 60.00 0.876 0.040 1.2 12/13/09 39,858,881.0 279.7 1,840.02,881.1 276 60.00 0.980 0.045 1.5 12/13/09 40,017,459.5 280.1 1,840.02,914.3 277 60.00 1.050 0.049 1.3 12/13/09 40,312,443.4 278.8 1,840.02,891.9 278 60.00 1.321 0.061 1.5 12/13/09 38,801,795.3 276.7 1,840.02,783.6 266 60.00 1.108 0.049 1.6 12/13/09 38,657,853.3 278.3 1,840.02,773.3 264 60.00 1.288 0.057 1.4 12/13/09 40,302,848.9 279.51,840.02,891.3 275 60.00 1.399 0.064 1.3 12/13/09 40,454,363.4 279.51,840.02,902.1 277 60.00 1.199 0.056 1.4 12/13/09 40,263,734.8 280.2 1,840.02,888.5 276 60.00 1.136 0.052 1.4 12/13/09 40,277,568.3 280.2 1,840.02,911.4 278 60.00 1.179 0.055 2.1 12/13/09 39,769,768.4 280.3 1,840.02,874.7 276 60.00 1.242 0.057 1.7 12/13/09 39,699,922.5 280.1 1,840.02,891.2 275 60.00 1.770 0.082 1.6 12/13/09 38,649,679.3 275.6 1,840.02,814.7 265 60.00 1.487 0.067 1.2 12/13/09 35,119,361.8 272.4 1,840.02,519.4 238 60.00 1.412 0.057 1.0 12/13/09 29,772,917.0 265.0 1,840.02,103.5 198 60.00 1.038 0.035 0.8 12/13/09 26,038,287.4 262.3 1,840.0 1,811.3 171 60.00 0.901 0.026 0.8 12/13/09 23,733,417.3 262.9 1,840.0 1,599.4 153 60.00 0.736 0.019 0.9 12/13/09 24,557,532.2 264.51,840.0 1,641.6 159 60.00 0.722 0.019 1.4 12/13/09 24,527,668.7 265.3 1,840.0 1,666.3 156 60.00 0.788 0.021 1.4 12/13/09 27,061,135.4 271.9 1,840.0 1,823.7 184 60.00 1.285 0.038 1.9 12/13/09 33,747,463.9 273.9 1,840.02,402.6 231 60.00 1.222 0.047 1.7 12/12/09 35,965,607.7 275.0 1,840.02,560.6 245 60.00 1.688 0.069 1.7 12/12/09 37,083,762.4 277.8 1,840.02,660.4 254 60.00 1.478 0.063 1.6 12/12/09 39,226,086.0 279.4 1,840.02,835.4 272 60.00 1.483 0.067 2.2 12/12/09 39,146,256.6 280.3 1,840.02,829.6 273 60.00 1.368 0.062 2.1 12/12/09 39,487,009.1 281.3 1,840.02,875.7 277 60.00 1.888 0.087 2.4 12/12/09 39,508,428.6 281.1 1,840.02,898.7 277 60.00 1.777 0.082 2.4 12/12/09 40,030,661.7 281.2 1,840.02,937.1 280 60.00 2.060 0.097 2.3 12/12/09 39,239,886.2 279.0 1,840.02,900.3 275 60.00 2.056 0.095 2.2 12/12/09 38,176,881.3 278.1 1,840.02,801.0 266 60.00 1.956 0.087 1.8 12/12/09 38,340,995.7 277.2 1,840.02,813.1 268 60.00 1.835 0.083 2.1 12/12/09 38,704,045.0 276.9 1,840.02,818.7 267 60.00 1.506 0.068 2.1 12/12/09 38,523,620.7 277.1 1,840.02,805.6 266 60.00 1.821 0.082 2.1 12/12/09 39,901,558.9 277.8 1,840.02,905.9 277 60.00 1.766 0.082 2.1 12/12/09 39,432,053.0 277.3 1,840.02,893.1 276 60.00 1.778 0.082 1.4 12/12/09 39,084,038.1 276.7 1,840.02,910.1 277 60.00 1.793 0.083 12/12/09 37,702,345.8 273.51,840.02,807.2 267 60.00 1.180 0.053

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 M 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 0.9 1.2 12/15/09 40,325,847.1 276.6 1,840.02,936.8 278 60.00 0.799 0.038 1.3 12/15/09 40,457,586.3 276.6 1,840.02,946.4 278 60.00 0.991 0.047 1.5 12/15/09 40,550,168.3 277.0 1,840.02,953.1 278 60.00 1.086 0.051 1.3 12/15/09 40,023,907.3 275.2 1,840.02,914.8 273 60.00 1.291 0.060 0.7 12/15/09 37,194,440.7 271.51,840.02,668.3 252 60.00 1.126 0.048 1.1 12/15/09 33,530,687.0 268.8 1,840.02,350.8 221 60.00 0.641 0.024 0.9 12/15/09 34,589,553.5 273.3 1,840.02,443.9 233 60.00 1.001 0.039 1.0 12/15/09 35,910,692.6 268.1 1,840.02,498.2 236 60.00 0.805 0.032 1.0 12/15/09 26,502,581.7 262.0 1,840.0 1,814.9 167 60.00 0.929 0.027 1.1 12/15/09 25,491,347.2 265.4 1,840.0 1,731.7 167 60.00 0.938 0.026 1.2 12/14/09 32,105,724.5 272.1 1,840.02,268.4 218 60.00 1.006 0.037 1.2 12/14/09 39,288,739.4 275.9 1,840.02,818.6 267 60.00 1.038 0.047 1.1 12/14/09 40,055,607.8 276.8 1,840.02,873.6 272 60.00 1.013 0.047 1.2 12/14/09 39,796,047.3 277.1 1,840.02,876.6 272 60.00 0.985 0.045 1.2 12/14/09 40,209,425.6 277.2 1,840.02,906.4 274 60.00 1.039 0.048 0.9 12/14/09 39,860,004.9 276.9 1,840.02,902.8 274 60.00 1.025 0.047 0.8 12/14/09 40,515,737.4 277.8 1,840.02,928.6 279 60.00 0.807 0.038 0.9 12/14/09 39,905,838.5 277.1 1,840.02,862.8 272 60.00 0.704 0.032 0.8 12/14/09 39,018,805.4 277.1 1,840.02,799.2 265 60.00 0.770 0.035 1.0 12/14/09 39,873,450.5 278.4 1,840.02,860.5 272 60.00 0.669 0.031 1.0 12/14/09 40,465,914.7 278.2 1,840.02,903.0 279 60.00 0.867 0.040 0.9 12/14/09 39,310,433.5 277.6 1,840.02,820.1 269 60.00 0.911 0.041 0.7 12/14/09 40,935,751.2 278.51,840.02,959.0 282 60.00 0.814 0.038 0.8 12/14/09 41,322,136.7 278.7 1,840.02,986.9 282 60.00 0.639 0.030 0.7 12/14/09 39,979,223.9 277.1 1,840.02,889.8 271 60.00 0.651 0.030 0.6 12/14/09 40,121,391.1 276.9 1,840.02,900.1 274 60.00 0.609 0.028 0.5 12/14/09 40,681,671.2 275.9 1,840.02,940.6 272 60.00 0.520 0.024 0.9 12/14/09 31,446,527.0 267.3 1,840.02,204.7 200 60.00 0.411 0.015 1.0 12/14/09 30,781,243.6 272.51,840.02,158.0 205 60.00 0.769 0.026 0.9 12/14/09 33,695,754.9 267.3 1,840.02,380.7 219 60.00 0.891 0.034 0.7 12/14/09 26,589,426.0 264.1 1,840.0 1,835.2 175 60.00 0.809 0.024 0.9 12/14/09 25,542,074.4 266.1 1,840.0 1,735.2 162 60.00 0.657 0.018 0.8 12/14/09 30,291,784.9 270.8 1,840.02,074.3 200 60.00 0.819 0.027 1.0 12/14/09 29,418,060.0 268.9 1,840.02,030.5 190 60.00 0.743 0.024 1.0 12/13/09 33,459,105.6 272.4 1,840.02,364.0 225 60.00 0.893 0.034 0.9 12/13/09 36,072,495.7 276.4 1,840.02,529.0 243 60.00 0.870 0.035 12/13/09 38,910,199.4 279.1 1,840.02,833.7 266 60.00 0.816 0.037

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 M 11:00 S S SC 12:00 S S S 13:00 S S SC 14:00 S S S 15:00 S S SC 16:00 C 17:00 ST ST STC 18:00 ST ST STC 19:00 C 20:00 21:00 22:00 1.9 1.9 12/16/09 39,434,829.2 276.1 1,840.02,850.5 271 60.00 1.617 0.073 1.9 12/16/09 40,274,612.0 276.3 1,840.02,933.1 278 60.00 1.601 0.075 1.7 12/16/09 39,960,566.2 276.8 1,840.02,888.5 276 60.00 1.632 0.076 2.0 12/16/09 40,358,661.1 278.51,840.02,961.1 281 60.00 1.437 0.068 2.0 12/16/09 40,305,889.7 277.8 1,840.02,979.1 282 60.00 1.650 0.078 2.2 12/16/09 40,162,546.3 277.1 1,840.02,990.4 282 60.00 1.637 0.078 1.9 12/16/09 39,405,613.0 276.0 1,840.02,955.5 277 60.00 1.837 0.087 1.9 12/16/09 39,457,392.0 276.3 1,840.02,937.8 275 60.00 1.554 0.073 1.9 12/16/09 39,385,226.1 276.2 1,840.02,911.1 274 60.00 1.569 0.073 1.9 12/16/09 39,962,998.3 277.0 1,840.02,932.1 276 60.00 1.580 0.074 1.9 12/16/09 39,619,671.1 276.51,840.02,928.4 275 60.00 1.570 0.073 1.5 12/16/09 40,210,724.7 276.9 1,840.02,950.3 276 60.00 1.587 0.075 1.3 12/16/09 40,371,828.6 276.4 1,840.02,984.0 278 60.00 1.274 0.061 1.3 12/16/09 40,360,185.4 276.0 1,840.02,961.2 278 60.00 1.080 0.051 1.4 12/16/09 40,628,008.9 276.2 1,840.02,980.9 281 60.00 1.069 0.051 0.8 12/16/09 40,454,282.6 274.7 1,840.02,968.1 280 60.00 1.214 0.058 0.6 12/16/09 36,889,766.0 267.0 1,840.02,666.5 246 60.00 0.678 0.029 1.3 12/16/09 26,626,999.5 265.2 1,840.0 1,837.8 175 60.00 0.562 0.017 1.0 12/16/09 32,035,843.0 270.6 1,840.02,246.0 218 60.00 1.145 0.041 1.1 12/16/09 36,409,540.8 271.3 1,840.02,612.0 243 60.00 0.873 0.036 1.4 12/16/09 32,668,882.8 268.8 1,840.02,308.1 217 60.00 0.958 0.036 1.5 12/16/09 33,856,234.9 272.3 1,840.02,447.2 232 60.00 1.203 0.047 1.4 12/16/09 37,992,378.7 274.8 1,840.02,746.2 260 60.00 1.322 0.058 1.2 12/15/09 39,527,766.8 274.2 1,840.02,878.7 272 60.00 1.166 0.053 1.0 12/15/09 38,747,124.0 275.51,840.02,800.7 268 60.00 1.060 0.048 1.0 12/15/09 40,804,431.2 276.8 1,840.02,993.8 283 60.00 0.838 0.040 1.1 12/15/09 40,870,989.3 277.0 1,840.02,998.7 283 60.00 0.859 0.041 0.8 12/15/09 40,716,032.4 276.7 1,840.03,009.4 282 60.00 0.965 0.046 0.7 12/15/09 41,008,545.4 275.3 1,840.02,986.5 282 60.00 0.697 0.033 0.6 12/15/09 40,554,936.6 274.9 1,840.02,953.5 279 60.00 0.596 0.028 0.8 12/15/09 40,371,369.9 274.8 1,840.02,940.1 276 60.00 0.556 0.026 0.7 12/15/09 40,056,601.1 274.9 1,840.02,895.4 273 60.00 0.649 0.030 0.7 12/15/09 40,976,932.9 275.51,840.02,961.9 280 60.00 0.584 0.028 0.8 12/15/09 40,943,725.9 276.0 1,840.02,959.5 279 60.00 0.602 0.029 0.8 12/15/09 40,790,317.5 275.9 1,840.02,948.4 278 60.00 0.679 0.032 1.0 12/15/09 40,890,728.5 276.6 1,840.02,955.7 279 60.00 0.651 0.031 12/15/09 40,424,039.2 275.8 1,840.02,965.9 279 60.00 0.852 0.040

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 M 09:00 M 10:00 S S S 11:00 S S S 12:00 S S SC 13:00 ST ST STC 14:00 MC 15:00 C 16:00 C 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 C 08:00 C 09:00 MC 10:00 S S SC 11:00 C 2.0 1.9 12/18/09 40,491,017.6 277.7 1,840.02,926.8 280 60.00 1.768 0.083 1.8 12/18/09 40,894,153.5 278.0 1,840.02,955.9 282 60.00 1.683 0.079 2.0 12/18/09 40,643,988.7 277.51,840.02,915.8 282 60.00 1.605 0.075 1.9 12/18/09 40,749,859.3 277.2 1,840.02,879.1 282 60.00 1.795 0.083 1.0 12/18/09 41,224,243.3 277.8 1,840.02,957.4 281 60.00 1.643 0.078 0.9 12/18/09 35,435,211.7 268.3 1,840.02,465.0 233 60.00 0.934 0.037 0.8 12/18/09 28,943,137.3 267.0 1,840.02,013.4 191 60.00 0.772 0.025 1.0 12/18/09 29,070,974.0 268.0 1,840.02,038.1 193 60.00 0.678 0.022 1.3 12/18/09 31,431,452.2 271.4 1,840.02,220.7 212 60.00 0.894 0.032 1.8 12/18/09 32,793,074.7 274.51,840.02,281.3 227 60.00 1.165 0.043 1.7 12/18/09 37,671,138.2 277.3 1,840.02,743.4 260 60.00 1.528 0.067 1.4 12/18/09 37,915,705.2 277.4 1,840.02,781.9 263 60.00 1.459 0.065 1.5 12/17/09 39,324,486.4 277.51,840.02,906.6 274 60.00 1.223 0.057 1.8 12/17/09 39,746,438.5 278.8 1,840.02,937.7 277 60.00 1.274 0.060 1.7 12/17/09 40,313,524.4 279.2 1,840.02,979.7 282 60.00 1.540 0.073 2.1 12/17/09 40,310,695.3 279.2 1,840.02,979.5 283 60.00 1.463 0.070 2.2 12/17/09 40,270,606.1 279.6 1,840.02,976.6 282 60.00 1.795 0.085 2.2 12/17/09 40,406,581.3 279.1 1,840.02,964.6 282 60.00 1.832 0.087 2.4 12/17/09 40,393,929.8 278.8 1,840.02,941.7 280 60.00 1.899 0.089 2.5 12/17/09 38,104,835.3 274.9 1,840.02,754.3 262 60.00 2.059 0.091 2.3 12/17/09 37,815,295.5 276.8 1,840.02,733.4 262 60.00 2.146 0.094 2.7 12/17/09 39,459,925.3 276.51,840.02,873.7 275 60.00 1.956 0.090 2.7 12/17/09 39,539,105.6 277.6 1,840.02,879.5 274 60.00 2.302 0.106 2.7 12/17/09 39,927,608.8 278.2 1,840.02,907.8 278 60.00 2.302 0.107 2.7 12/17/09 40,356,437.7 278.4 1,840.02,895.1 277 60.00 2.326 0.108 3.1 12/17/09 40,589,250.6 279.7 1,840.02,911.8 278 60.00 2.332 0.109 3.0 12/17/09 40,589,562.0 279.3 1,840.02,934.0 280 60.00 2.655 0.125 2.9 12/17/09 40,402,024.6 278.8 1,840.02,920.4 279 60.00 2.616 0.123 2.0 12/17/09 40,410,584.4 277.1 1,840.02,921.0 277 60.00 2.519 0.117 1.7 12/17/09 33,863,145.0 266.7 1,840.02,392.5 222 60.00 1.796 0.069 2.2 12/17/09 26,226,615.3 267.1 1,840.0 1,810.2 177 60.00 1.556 0.045 2.0 12/17/09 33,863,237.0 272.0 1,840.02,355.7 231 60.00 1.984 0.074 1.8 12/17/09 35,689,657.9 271.4 1,840.02,579.8 245 60.00 1.703 0.070 2.1 12/17/09 33,562,447.3 270.4 1,840.02,371.2 230 60.00 1.605 0.061 2.1 12/17/09 31,851,742.2 270.0 1,840.02,267.7 217 60.00 1.810 0.066 2.3 12/17/09 36,324,566.7 274.6 1,840.02,566.4 247 60.00 1.820 0.075 12/16/09 39,949,280.9 275.7 1,840.02,909.3 277 60.00 1.976 0.092

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 2.4 1.8 12/20/09 35,112,724.0 276.6 1,840.02,461.7 239 60.00 2.126 0.084 2.8 12/19/09 32,751,379.5 274.6 1,840.02,296.1 220 60.00 1.616 0.059 2.6 12/19/09 37,806,208.2 280.6 1,840.02,732.7 262 60.00 2.391 0.104 2.7 12/19/09 40,109,262.8 281.8 1,840.02,899.2 277 60.00 2.246 0.104 2.5 12/19/09 40,227,535.9 281.7 1,840.02,907.8 277 60.00 2.314 0.107 3.2 12/19/09 40,252,328.3 281.51,840.02,865.8 277 60.00 2.200 0.101 3.3 12/19/09 40,289,880.8 282.8 1,840.02,846.6 278 60.00 2.832 0.129 3.1 12/19/09 40,209,684.5 281.7 1,840.02,840.9 277 60.00 2.919 0.133 2.7 12/19/09 39,459,542.0 278.7 1,840.02,787.9 270 60.00 2.772 0.123 3.0 12/19/09 38,759,514.5 279.2 1,840.02,738.5 265 60.00 2.407 0.105 3.6 12/19/09 39,885,895.1 279.7 1,840.02,818.0 274 60.00 2.685 0.121 3.8 12/19/09 40,594,704.4 279.4 1,840.02,868.1 279 60.00 3.152 0.145 3.7 12/19/09 39,971,779.5 279.8 1,840.02,824.1 274 60.00 3.357 0.151 3.9 12/19/09 40,955,716.8 281.1 1,840.02,915.9 281 60.00 3.231 0.150 4.2 12/19/09 40,733,433.5 280.6 1,840.02,922.2 282 60.00 3.359 0.157 3.3 12/19/09 40,707,439.4 279.0 1,840.02,898.2 280 60.00 3.684 0.170 4.1 12/19/09 37,235,164.4 274.9 1,840.02,570.0 250 60.00 2.932 0.121 3.8 12/19/09 38,688,007.3 276.8 1,840.02,712.4 262 60.00 3.676 0.160 2.2 12/19/09 38,060,966.4 272.1 1,840.02,689.1 254 60.00 3.386 0.146 1.6 12/19/09 29,977,891.9 263.9 1,840.02,020.3 195 60.00 2.005 0.065 1.8 12/19/09 26,099,057.9 263.4 1,840.0 1,702.1 168 60.00 1.503 0.041 2.1 12/19/09 27,057,433.5 264.9 1,840.0 1,764.6 173 60.00 1.699 0.048 1.8 12/19/09 29,169,175.9 269.3 1,840.0 1,902.3 193 60.00 1.980 0.060 1.8 12/19/09 33,671,560.1 269.8 1,840.02,342.4 223 60.00 1.641 0.061 1.6 12/19/09 33,233,864.6 272.1 1,840.02,311.9 226 60.00 1.642 0.060 1.8 12/18/09 34,765,035.4 272.7 1,840.02,418.4 235 60.00 1.420 0.055 2.0 12/18/09 38,408,903.9 277.0 1,840.02,755.4 264 60.00 1.541 0.068 2.0 12/18/09 39,892,467.5 279.2 1,840.02,883.5 278 60.00 1.755 0.081 2.0 12/18/09 40,216,620.2 278.51,840.02,950.7 282 60.00 1.724 0.081 1.8 12/18/09 39,853,123.9 278.0 1,840.02,924.0 279 60.00 1.721 0.081 1.5 12/18/09 39,943,122.6 277.1 1,840.02,908.9 281 60.00 1.573 0.073 1.7 12/18/09 39,901,253.6 278.3 1,840.02,927.5 279 60.00 1.268 0.059 1.8 12/18/09 39,802,036.4 277.51,840.02,920.3 278 60.00 1.453 0.068 2.1 12/18/09 39,449,878.9 277.1 1,840.02,873.0 274 60.00 1.520 0.070 2.0 12/18/09 40,404,094.0 278.51,840.02,898.5 277 60.00 1.787 0.083 2.1 12/18/09 39,813,414.6 277.4 1,840.02,899.4 276 60.00 1.729 0.080 12/18/09 40,275,753.0 277.8 1,840.02,911.3 279 60.00 1.802 0.084

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 C 10:00 C 11:00 C 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 3.6 4.3 12/21/09 40,525,268.7 285.51,840.02,929.3 275 60.00 3.134 0.147 4.8 12/21/09 41,102,351.8 285.6 1,840.02,971.0 280 60.00 3.688 0.176 3.9 12/21/09 40,448,563.3 284.6 1,840.02,945.7 277 60.00 4.109 0.194 3.5 12/21/09 40,961,775.4 283.4 1,840.02,983.1 282 60.00 3.348 0.160 3.0 12/21/09 40,692,165.6 282.2 1,840.02,963.4 282 60.00 3.020 0.144 3.4 12/21/09 41,693,663.8 285.2 1,840.03,013.8 282 60.00 2.628 0.127 3.2 12/21/09 40,936,339.3 284.4 1,840.03,003.5 281 60.00 2.865 0.138 3.4 12/21/09 38,858,148.6 278.51,840.02,787.6 261 60.00 2.775 0.124 3.0 12/21/09 36,008,643.4 279.7 1,840.02,563.7 243 60.00 2.997 0.122 3.5 12/21/09 37,516,719.2 278.4 1,840.02,650.7 251 60.00 2.680 0.113 3.5 12/21/09 38,225,797.9 280.4 1,840.02,680.0 255 60.00 3.158 0.135 3.5 12/21/09 38,106,815.7 280.4 1,840.02,692.3 258 60.00 3.059 0.132 3.5 12/21/09 37,819,504.9 281.3 1,840.02,692.6 256 60.00 3.024 0.130 3.4 12/21/09 38,986,711.0 282.7 1,840.02,796.9 266 60.00 3.010 0.134 3.2 12/20/09 38,849,783.3 280.6 1,840.02,787.1 265 60.00 3.009 0.134 3.0 12/20/09 38,611,689.9 283.1 1,840.02,749.0 265 60.00 2.777 0.122 2.8 12/20/09 40,253,451.4 283.7 1,840.02,909.6 278 60.00 2.597 0.120 3.3 12/20/09 40,694,938.7 283.9 1,840.02,941.5 282 60.00 2.456 0.116 3.3 12/20/09 40,517,510.8 284.7 1,840.02,928.7 280 60.00 2.830 0.132 3.0 12/20/09 40,557,722.7 283.7 1,840.02,931.6 282 60.00 2.804 0.132 2.9 12/20/09 41,225,764.5 284.8 1,840.02,957.5 283 60.00 2.597 0.123 3.1 12/20/09 40,188,620.9 283.3 1,840.02,926.8 278 60.00 2.467 0.115 3.3 12/20/09 39,743,531.7 282.1 1,840.02,872.8 273 60.00 2.655 0.122 3.6 12/20/09 39,576,568.0 281.4 1,840.02,839.2 271 60.00 2.892 0.131 3.2 12/20/09 39,195,965.0 282.2 1,840.02,811.9 266 60.00 3.134 0.140 3.4 12/20/09 39,095,758.1 282.1 1,840.02,826.0 269 60.00 2.790 0.126 3.2 12/20/09 38,563,180.4 281.4 1,840.02,766.5 267 60.00 2.919 0.130 4.1 12/20/09 39,704,616.2 282.7 1,840.02,848.4 275 60.00 2.793 0.127 3.6 12/20/09 39,205,167.8 283.7 1,840.02,812.5 271 60.00 3.600 0.162 3.4 12/20/09 40,133,186.3 283.3 1,840.02,879.1 279 60.00 3.151 0.145 3.5 12/20/09 40,251,696.1 283.9 1,840.02,865.8 273 60.00 2.992 0.137 3.0 12/20/09 35,980,521.5 277.6 1,840.02,542.1 242 60.00 3.119 0.127 2.0 12/20/09 31,904,872.0 272.3 1,840.02,271.5 217 60.00 2.579 0.094 2.4 12/20/09 26,697,327.1 269.0 1,840.0 1,857.2 179 60.00 1.789 0.053 2.2 12/20/09 30,677,621.7 274.3 1,840.02,100.8 211 60.00 2.199 0.074 2.1 12/20/09 34,413,513.6 273.1 1,840.02,412.7 233 60.00 1.974 0.076 12/20/09 31,074,964.0 274.1 1,840.02,161.7 212 60.00 1.889 0.065

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 1.5 2.0 12/23/09 25,261,448.3 266.8 1,840.0 1,688.6 162 60.00 1.402 0.038 2.0 12/23/09 27,458,121.1 268.1 1,840.0 1,835.5 174 60.00 1.829 0.054 2.4 12/23/09 29,735,418.6 273.0 1,840.02,036.2 198 60.00 1.777 0.058 2.9 12/22/09 31,008,528.8 276.51,840.02,207.7 211 60.00 2.109 0.075 2.9 12/22/09 38,087,389.9 282.51,840.02,773.7 261 60.00 2.450 0.109 3.8 12/22/09 40,349,367.9 285.0 1,840.02,938.5 278 60.00 2.473 0.116 4.4 12/22/09 41,131,931.9 288.8 1,840.02,995.5 282 60.00 3.224 0.154 4.2 12/22/09 40,800,030.7 288.2 1,840.02,993.5 280 60.00 3.785 0.181 4.1 12/22/09 41,207,387.2 287.3 1,840.03,000.9 282 60.00 3.575 0.172 4.3 12/22/09 40,847,073.6 286.51,840.02,974.7 280 60.00 3.473 0.165 4.1 12/22/09 40,878,048.0 285.51,840.02,954.8 279 60.00 3.669 0.174 4.2 12/22/09 40,150,409.4 284.51,840.02,880.3 274 60.00 3.546 0.163 4.6 12/22/09 40,406,866.7 284.1 1,840.02,898.8 276 60.00 3.635 0.169 4.5 12/22/09 40,174,287.0 284.0 1,840.02,882.0 274 60.00 3.950 0.182 4.2 12/22/09 39,996,764.1 283.1 1,840.02,891.1 274 60.00 3.905 0.181 4.2 12/22/09 40,038,700.5 284.3 1,840.02,894.1 274 60.00 3.590 0.166 4.4 12/22/09 41,173,308.4 284.8 1,840.02,953.7 281 60.00 3.628 0.171 5.0 12/22/09 41,310,696.7 284.51,840.02,963.6 280 60.00 3.831 0.181 4.1 12/22/09 40,992,251.0 283.6 1,840.02,963.0 279 60.00 4.279 0.203 3.1 12/22/09 38,945,394.7 277.2 1,840.02,772.7 260 60.00 3.623 0.161 3.5 12/22/09 31,800,296.6 273.0 1,840.02,229.5 212 60.00 2.779 0.099 2.7 12/22/09 34,817,605.8 277.51,840.02,403.2 232 60.00 3.178 0.122 3.6 12/22/09 35,740,589.6 276.7 1,840.02,466.9 234 60.00 2.444 0.096 3.3 12/22/09 36,692,600.9 279.51,840.02,612.4 246 60.00 3.183 0.133 2.4 12/22/09 35,321,197.4 277.3 1,840.02,495.5 234 60.00 2.947 0.118 2.8 12/22/09 34,624,657.8 276.51,840.02,446.3 230 60.00 2.098 0.082 3.1 12/22/09 35,818,181.4 280.2 1,840.02,511.2 238 60.00 2.485 0.100 3.0 12/21/09 39,521,015.7 281.51,840.02,813.7 264 60.00 2.671 0.120 2.7 12/21/09 39,486,580.9 283.51,840.02,811.3 269 60.00 2.633 0.118 3.1 12/21/09 40,506,962.4 283.8 1,840.02,905.9 274 60.00 2.357 0.109 3.0 12/21/09 41,441,470.3 284.3 1,840.02,950.4 281 60.00 2.703 0.128 3.6 12/21/09 41,567,002.3 285.4 1,840.02,959.4 281 60.00 2.655 0.125 3.6 12/21/09 41,268,020.5 286.4 1,840.02,983.0 282 60.00 3.131 0.149 3.2 12/21/09 40,919,852.4 285.2 1,840.03,002.3 282 60.00 3.103 0.149 3.4 12/21/09 39,826,048.8 283.8 1,840.02,900.4 271 60.00 2.768 0.128 3.7 12/21/09 39,743,503.8 284.4 1,840.02,894.4 270 60.00 2.899 0.134 12/21/09 40,434,716.1 283.7 1,840.02,922.7 274 60.00 3.169 0.148

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 2.7 2.3 12/24/09 33,135,312.6 273.1 1,840.02,251.0 218 60.00 2.463 0.089 2.1 12/24/09 31,830,258.9 272.0 1,840.02,214.3 209 60.00 2.047 0.073 2.7 12/24/09 30,331,242.7 274.3 1,840.02,159.4 203 60.00 1.829 0.063 3.4 12/24/09 35,792,200.7 280.3 1,840.02,567.7 245 60.00 2.323 0.095 4.1 12/24/09 39,484,821.5 281.2 1,840.02,854.1 269 60.00 2.946 0.134 3.4 12/24/09 39,416,252.6 280.9 1,840.02,827.7 268 60.00 3.587 0.162 1.5 12/24/09 36,136,315.8 270.9 1,840.02,533.4 237 60.00 3.045 0.124 2.7 12/24/09 27,155,398.4 265.51,840.0 1,844.8 175 60.00 1.402 0.041 2.9 12/24/09 28,675,141.2 269.7 1,840.0 1,948.0 192 60.00 2.505 0.078 2.2 12/24/09 31,466,623.5 268.3 1,840.02,189.0 208 60.00 2.592 0.091 1.8 12/24/09 29,597,265.5 265.4 1,840.02,058.9 193 60.00 1.925 0.064 2.0 12/24/09 26,363,261.2 264.9 1,840.0 1,791.0 169 60.00 1.686 0.048 1.8 12/24/09 25,772,795.3 265.1 1,840.0 1,806.9 164 60.00 1.767 0.051 1.7 12/24/09 25,640,586.7 263.51,840.0 1,811.6 160 60.00 1.624 0.047 2.3 12/24/09 24,700,149.8 266.6 1,840.0 1,664.6 162 60.00 1.604 0.043 2.0 12/24/09 30,873,313.2 269.1 1,840.02,097.4 201 60.00 2.121 0.071 1.6 12/23/09 29,827,789.8 267.7 1,840.02,075.0 192 60.00 1.831 0.061 2.4 12/23/09 27,581,350.9 272.9 1,840.0 1,888.7 184 60.00 1.430 0.043 2.5 12/23/09 38,582,955.0 280.1 1,840.02,788.9 265 60.00 2.090 0.093 2.7 12/23/09 40,209,675.8 280.8 1,840.02,928.3 278 60.00 2.101 0.099 3.0 12/23/09 40,849,760.8 281.2 1,840.02,974.9 281 60.00 2.302 0.109 2.8 12/23/09 41,150,871.9 282.7 1,840.02,996.9 281 60.00 2.566 0.123 3.0 12/23/09 40,770,660.0 282.6 1,840.02,969.2 280 60.00 2.396 0.114 3.2 12/23/09 39,933,400.1 281.2 1,840.02,908.2 273 60.00 2.567 0.119 3.4 12/23/09 39,588,302.2 281.7 1,840.02,883.0 270 60.00 2.730 0.126 4.5 12/23/09 39,659,202.1 282.7 1,840.02,888.2 270 60.00 2.900 0.134 6.1 12/23/09 39,986,543.7 282.8 1,840.02,912.1 274 60.00 3.840 0.179 6.6 12/23/09 40,026,169.2 282.6 1,840.02,936.7 274 60.00 5.221 0.245 7.0 12/23/09 40,207,373.2 282.9 1,840.02,950.0 274 60.00 5.596 0.264 4.9 12/23/09 40,817,635.2 283.3 1,840.02,994.8 279 60.00 5.942 0.285 4.8 12/23/09 40,533,275.0 283.1 1,840.02,929.8 278 60.00 4.213 0.197 3.7 12/23/09 40,589,209.7 282.3 1,840.02,955.9 279 60.00 4.092 0.193 2.4 12/23/09 38,877,188.2 276.1 1,840.02,852.4 264 60.00 3.157 0.144 2.1 12/23/09 31,469,022.6 268.1 1,840.02,223.4 203 60.00 2.072 0.074 1.0 12/23/09 28,554,124.7 267.1 1,840.0 1,939.8 184 60.00 1.883 0.058 1.1 12/23/09 28,643,908.9 264.6 1,840.0 1,930.4 180 60.00 0.912 0.028 12/23/09 25,098,890.4 264.3 1,840.0 1,650.5 159 60.00 1.004 0.026

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 1.3 1.4 12/26/09 30,555,778.3 272.2 1,840.02,158.8 205 60.00 1.106 0.038 2.2 12/26/09 29,440,038.4 272.4 1,840.02,032.0 198 60.00 1.246 0.041 2.0 12/26/09 31,885,261.7 274.2 1,840.02,218.1 215 60.00 1.968 0.070 2.4 12/26/09 31,765,192.2 273.8 1,840.02,227.0 215 60.00 1.817 0.065 1.9 12/26/09 33,255,780.8 274.3 1,840.02,331.5 225 60.00 2.099 0.078 2.3 12/25/09 29,439,217.7 272.3 1,840.02,079.9 200 60.00 1.709 0.057 2.3 12/25/09 33,922,204.4 278.1 1,840.02,378.2 233 60.00 2.046 0.078 2.3 12/25/09 38,178,583.8 281.2 1,840.02,676.7 260 60.00 2.018 0.087 2.3 12/25/09 39,664,933.2 281.51,840.02,824.0 272 60.00 2.058 0.093 3.0 12/25/09 38,322,049.9 278.51,840.02,686.7 257 60.00 2.095 0.090 2.9 12/25/09 34,823,062.8 277.4 1,840.02,460.3 235 60.00 2.682 0.105 2.5 12/25/09 35,504,489.1 276.2 1,840.02,527.7 238 60.00 2.540 0.103 1.4 12/25/09 35,308,318.0 273.3 1,840.02,513.8 236 60.00 2.227 0.090 1.5 12/25/09 30,258,942.2 269.9 1,840.02,137.9 203 60.00 1.244 0.043 1.9 12/25/09 29,874,071.7 269.6 1,840.02,094.4 197 60.00 1.354 0.045 2.8 12/25/09 29,599,221.6 270.8 1,840.02,075.1 195 60.00 1.717 0.057 3.3 12/25/09 30,194,970.8 272.1 1,840.02,067.7 200 60.00 2.552 0.084 3.1 12/25/09 34,350,660.4 272.9 1,840.02,389.6 229 60.00 2.985 0.114 2.0 12/25/09 35,017,828.6 273.0 1,840.02,436.0 232 60.00 2.782 0.109 1.1 12/25/09 31,671,280.7 268.2 1,840.02,220.4 209 60.00 1.738 0.062 1.8 12/25/09 27,827,949.7 265.3 1,840.0 1,905.6 181 60.00 1.030 0.031 1.3 12/25/09 29,699,854.5 264.1 1,840.02,001.5 196 60.00 1.631 0.052 1.5 12/25/09 26,292,375.9 260.9 1,840.0 1,757.6 166 60.00 1.250 0.035 1.6 12/25/09 24,536,857.1 261.1 1,840.0 1,586.9 154 60.00 1.474 0.037 1.8 12/25/09 24,916,498.8 261.3 1,840.0 1,597.9 153 60.00 1.548 0.040 2.2 12/25/09 24,321,195.0 260.9 1,840.0 1,572.9 151 60.00 1.768 0.045 2.1 12/25/09 23,586,113.7 261.0 1,840.0 1,551.0 151 60.00 2.108 0.052 2.1 12/25/09 24,348,089.9 261.8 1,840.0 1,614.4 154 60.00 1.965 0.051 1.9 12/25/09 25,122,249.6 263.6 1,840.0 1,665.7 158 60.00 1.952 0.052 1.8 12/24/09 25,773,492.4 264.3 1,840.0 1,722.9 162 60.00 1.798 0.050 2.5 12/24/09 26,497,105.4 266.1 1,840.0 1,742.5 169 60.00 1.723 0.048 2.6 12/24/09 28,990,990.0 271.8 1,840.0 1,969.5 195 60.00 2.270 0.072 2.7 12/24/09 32,074,606.3 270.6 1,840.02,248.7 212 60.00 2.299 0.083 1.9 12/24/09 31,267,680.8 270.7 1,840.02,175.2 207 60.00 2.451 0.085 1.6 12/24/09 29,930,511.4 266.9 1,840.02,114.7 197 60.00 1.708 0.058 2.0 12/24/09 25,189,565.4 268.6 1,840.0 1,766.0 171 60.00 1.387 0.039 12/24/09 31,185,265.2 271.1 1,840.02,169.4 204 60.00 1.784 0.062

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 0.8 0.7 12/27/09 27,182,587.2 264.8 1,840.0 1,905.8 180 60.00 0.733 0.022 0.7 12/27/09 26,180,746.1 264.6 1,840.0 1,835.5 173 60.00 0.639 0.019 0.7 12/27/09 27,022,658.1 266.0 1,840.0 1,894.5 178 60.00 0.635 0.019 0.8 12/27/09 27,360,658.4 266.4 1,840.0 1,888.5 179 60.00 0.658 0.020 1.0 12/27/09 27,771,949.8 266.6 1,840.0 1,916.9 180 60.00 0.713 0.022 0.8 12/27/09 26,741,268.7 265.7 1,840.0 1,874.8 179 60.00 0.917 0.027 0.8 12/27/09 27,144,467.8 265.9 1,840.0 1,903.0 181 60.00 0.701 0.021 0.8 12/27/09 27,139,150.1 266.51,840.0 1,873.2 177 60.00 0.713 0.021 0.9 12/27/09 27,262,815.0 266.2 1,840.0 1,852.1 176 60.00 0.749 0.022 1.4 12/27/09 26,827,767.7 265.2 1,840.0 1,808.0 172 60.00 0.796 0.023 1.4 12/27/09 26,503,313.6 264.51,840.0 1,800.5 174 60.00 1.247 0.036 1.2 12/27/09 26,406,323.4 263.8 1,840.0 1,779.5 171 60.00 1.290 0.037 1.2 12/27/09 25,351,674.8 263.51,840.0 1,763.6 163 60.00 1.118 0.032 1.2 12/27/09 24,131,227.7 264.6 1,840.0 1,639.3 153 60.00 1.084 0.028 1.2 12/27/09 25,243,775.7 265.3 1,840.0 1,714.9 161 60.00 1.057 0.029 1.0 12/27/09 25,847,660.9 265.4 1,840.0 1,770.0 165 60.00 1.091 0.031 1.0 12/27/09 25,431,463.9 265.3 1,840.0 1,755.3 166 60.00 0.938 0.026 0.9 12/27/09 26,260,707.1 265.4 1,840.0 1,826.9 174 60.00 0.929 0.027 0.9 12/26/09 25,474,583.4 265.51,840.0 1,813.7 169 60.00 0.771 0.022 0.9 12/26/09 26,374,061.7 267.3 1,840.0 1,820.4 174 60.00 0.830 0.024 0.9 12/26/09 27,518,326.3 267.8 1,840.0 1,884.4 180 60.00 0.860 0.026 1.0 12/26/09 27,166,862.9 268.0 1,840.0 1,889.9 180 60.00 0.842 0.025 0.9 12/26/09 28,300,107.3 268.6 1,840.0 1,968.7 191 60.00 0.875 0.028 0.6 12/26/09 29,746,569.3 269.8 1,840.02,020.9 199 60.00 0.811 0.026 0.7 12/26/09 31,501,099.9 274.0 1,840.02,208.5 213 60.00 0.496 0.018 1.1 12/26/09 32,748,069.2 275.4 1,840.02,331.5 220 60.00 0.619 0.023 2.0 12/26/09 32,643,651.8 276.51,840.02,288.6 219 60.00 0.990 0.036 2.3 12/26/09 34,039,738.1 280.0 1,840.02,423.5 232 60.00 1.767 0.068 2.1 12/26/09 36,384,309.0 283.1 1,840.02,649.7 249 60.00 1.953 0.083 2.3 12/26/09 38,563,241.0 283.1 1,840.02,745.5 265 60.00 1.864 0.082 2.2 12/26/09 39,057,200.2 282.51,840.02,759.5 268 60.00 2.038 0.090 1.5 12/26/09 39,425,085.6 280.9 1,840.02,806.9 273 60.00 1.920 0.086 1.4 12/26/09 39,005,691.4 279.1 1,840.02,777.1 268 60.00 1.302 0.058 1.6 12/26/09 35,531,070.4 276.8 1,840.02,491.0 242 60.00 1.208 0.048 1.3 12/26/09 38,368,005.7 278.6 1,840.02,731.6 263 60.00 1.431 0.062 1.1 12/26/09 36,150,012.2 274.2 1,840.02,534.4 245 60.00 1.130 0.046 12/26/09 31,841,944.8 271.8 1,840.02,249.7 214 60.00 0.941 0.034

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 M 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 2.7 2.3 12/29/09 40,620,099.4 278.51,840.02,869.9 275 60.00 2.390 0.110 2.9 12/29/09 39,662,048.7 279.2 1,840.02,888.4 268 60.00 2.003 0.093 2.9 12/29/09 40,035,889.8 278.6 1,840.02,872.1 269 60.00 2.527 0.116 3.2 12/29/09 40,421,736.3 279.6 1,840.02,877.9 275 60.00 2.578 0.119 2.9 12/29/09 41,095,745.1 279.8 1,840.02,903.5 282 60.00 2.797 0.130 2.9 12/29/09 40,828,975.6 280.3 1,840.02,929.0 281 60.00 2.486 0.116 2.5 12/29/09 40,387,117.0 280.8 1,840.02,919.3 279 60.00 2.460 0.115 3.8 12/28/09 40,801,840.0 281.1 1,840.02,927.1 281 60.00 2.215 0.104 4.1 12/28/09 40,504,983.8 281.8 1,840.02,883.8 277 60.00 3.340 0.154 3.8 12/28/09 41,308,031.8 281.3 1,840.02,918.5 282 60.00 3.652 0.170 3.3 12/28/09 41,102,176.1 280.7 1,840.02,903.9 281 60.00 3.341 0.155 3.2 12/28/09 41,007,709.0 280.7 1,840.02,919.6 281 60.00 2.875 0.134 2.8 12/28/09 41,360,937.3 281.3 1,840.02,944.7 282 60.00 2.765 0.130 2.5 12/28/09 40,729,614.3 281.0 1,840.02,944.1 282 60.00 2.409 0.114 3.3 12/28/09 39,027,985.2 279.2 1,840.02,799.8 268 60.00 2.147 0.096 3.1 12/28/09 39,828,169.2 280.8 1,840.02,857.2 275 60.00 2.883 0.131 3.2 12/28/09 40,347,232.3 280.3 1,840.02,872.5 278 60.00 2.748 0.126 3.1 12/28/09 41,122,320.7 280.2 1,840.02,860.7 276 60.00 2.911 0.133 2.9 12/28/09 41,862,955.1 281.1 1,840.02,889.5 278 60.00 2.837 0.131 2.5 12/28/09 41,346,086.8 281.0 1,840.02,898.7 283 60.00 2.597 0.120 2.5 12/28/09 40,266,757.1 280.2 1,840.02,845.0 274 60.00 2.175 0.099 2.7 12/28/09 40,344,470.0 280.51,840.02,850.4 275 60.00 2.172 0.099 2.2 12/28/09 40,698,625.7 280.51,840.02,831.2 274 60.00 2.439 0.111 1.2 12/28/09 40,453,197.1 279.9 1,840.02,836.1 274 60.00 1.995 0.090 1.1 12/28/09 36,773,635.5 271.9 1,840.02,518.2 241 60.00 1.082 0.044 1.3 12/28/09 27,210,080.5 268.1 1,840.0 1,833.7 173 60.00 0.986 0.029 1.5 12/28/09 28,764,439.2 267.8 1,840.02,001.0 188 60.00 1.199 0.038 2.2 12/28/09 27,282,343.0 270.3 1,840.0 1,838.6 185 60.00 1.429 0.042 2.4 12/28/09 31,523,868.0 275.1 1,840.02,193.0 226 60.00 1.982 0.070 1.5 12/28/09 36,458,255.7 276.9 1,840.02,595.7 250 60.00 2.077 0.086 0.8 12/28/09 36,933,732.8 271.9 1,840.02,669.7 252 60.00 1.254 0.053 0.7 12/27/09 28,155,880.3 264.9 1,840.0 1,974.0 186 60.00 0.729 0.023 0.5 12/27/09 27,097,352.4 265.0 1,840.0 1,885.0 180 60.00 0.611 0.018 0.5 12/27/09 27,300,279.0 266.2 1,840.0 1,884.3 180 60.00 0.437 0.013 0.5 12/27/09 27,674,508.9 266.3 1,840.0 1,895.1 180 60.00 0.436 0.013 0.8 12/27/09 27,562,381.6 266.3 1,840.0 1,917.4 180 60.00 0.463 0.014 12/27/09 27,196,485.3 265.2 1,840.0 1,877.1 179 60.00 0.716 0.022

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

07:00 08:00 09:00 10:00 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00 00:00 01:00 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 S S S 11:00 C 12:00 C 13:00 14:00 15:00 16:00 17:00 18:00 19:00 4.1 3.7 12/30/09 40,359,377.7 283.6 1,840.02,939.2 277 60.00 3.549 0.167 3.2 12/30/09 40,152,077.2 282.4 1,840.02,967.8 280 60.00 3.124 0.148 3.1 12/30/09 40,397,925.6 282.4 1,840.03,007.9 282 60.00 2.693 0.129 3.2 12/30/09 39,387,878.2 280.51,840.02,911.3 275 60.00 2.630 0.122 3.7 12/30/09 39,272,110.2 281.9 1,840.02,902.7 272 60.00 2.737 0.127 3.4 12/30/09 40,021,932.9 282.3 1,840.02,958.1 276 60.00 3.089 0.146 3.5 12/30/09 40,023,054.2 282.1 1,840.02,980.0 280 60.00 2.811 0.134 2.6 12/30/09 40,200,673.5 281.4 1,840.02,993.2 282 60.00 2.895 0.139 2.3 12/30/09 40,450,157.0 280.6 1,840.02,989.8 283 60.00 2.179 0.104 2.0 12/30/09 40,257,965.7 281.0 1,840.02,953.7 282 60.00 1.940 0.092 2.8 12/30/09 40,830,903.6 281.6 1,840.02,973.6 282 60.00 1.696 0.081 2.9 12/30/09 40,279,055.5 280.7 1,840.02,977.1 281 60.00 2.343 0.112 2.8 12/30/09 40,330,059.6 280.3 1,840.02,980.9 282 60.00 2.454 0.117 2.5 12/30/09 39,962,291.1 279.2 1,840.02,953.7 279 60.00 2.336 0.110 1.7 12/30/09 38,248,982.4 275.7 1,840.02,764.7 261 60.00 2.124 0.094 1.4 12/30/09 34,350,044.0 273.0 1,840.02,426.9 232 60.00 1.525 0.059 1.5 12/30/09 34,502,671.8 274.9 1,840.02,475.2 236 60.00 1.199 0.047 1.7 12/30/09 36,389,329.2 276.8 1,840.02,650.1 252 60.00 1.284 0.054 2.9 12/30/09 36,669,055.6 278.3 1,840.02,690.4 253 60.00 1.419 0.061 2.9 12/30/09 38,528,533.6 281.51,840.02,826.9 268 60.00 2.439 0.111 2.7 12/29/09 39,792,459.7 281.3 1,840.02,962.8 278 60.00 2.446 0.116 2.5 12/29/09 39,719,878.5 280.1 1,840.02,935.8 278 60.00 2.273 0.107 1.8 12/29/09 39,406,740.6 279.8 1,840.02,912.7 276 60.00 2.066 0.096 1.8 12/29/09 39,722,209.5 280.8 1,840.02,957.6 279 60.00 1.525 0.072 1.9 12/29/09 39,903,261.3 281.0 1,840.02,949.4 280 60.00 1.506 0.071 3.1 12/29/09 39,941,791.3 281.7 1,840.02,952.2 280 60.00 1.625 0.077 3.4 12/29/09 40,513,410.0 282.7 1,840.02,950.4 281 60.00 2.673 0.126 3.4 12/29/09 40,036,229.6 281.0 1,840.02,915.7 275 60.00 2.940 0.137 2.9 12/29/09 40,022,961.4 280.51,840.02,893.0 275 60.00 2.892 0.134 2.7 12/29/09 40,763,348.6 279.9 1,840.02,968.6 281 60.00 2.484 0.118 2.5 12/29/09 40,742,827.4 279.9 1,840.02,945.0 280 60.00 2.299 0.109 3.0 12/29/09 40,222,509.6 279.9 1,840.02,951.1 278 60.00 2.171 0.102 3.1 12/29/09 40,718,949.1 279.6 1,840.02,965.4 280 60.00 2.575 0.122 2.4 12/29/09 41,227,471.7 278.51,840.02,957.6 280 60.00 2.740 0.129 2.0 12/29/09 40,874,949.7 278.9 1,840.02,910.1 277 60.00 2.132 0.099 2.2 12/29/09 40,620,064.0 279.1 1,840.02,936.1 275 60.00 1.739 0.082 12/29/09 40,656,632.4 278.6 1,840.02,872.5 273 60.00 1.949 0.090

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

20:00 21:00 22:00 23:00 00:00 S S S 01:00 S S S 02:00 C 03:00 04:00 C 05:00 C C 06:00 07:00 08:00 09:00 10:00 11:00 12:00 13:00 14:00 15:00 16:00 17:00 18:00 19:00 20:00 21:00 22:00 23:00

7724 7724 7724 7724 7724 7724 Included Data Points7724 7720 7724 847.08624,203.8 107.162 0.513 12.5 Summation262,546,775,374.42,109,315.614,212,160.018,593,451.01,751,771463,014.00 0.000 0.000 0.0 Maximum44,758,753.8 310.7 1,840.03,268.2 307 60.00 0.110 3.1 Minimum18,421,536.8 66.8 1,840.0 1.0 0 2.00 4.5

Average33,991,037.7 273.2 1,840.02,407.2 227 59.94 4.3 12/31/09 39,746,001.6 280.9 1,840.02,872.9 273 60.00 3.873 0.178 3.8 12/31/09 39,840,050.3 280.1 1,840.02,879.7 273 60.00 3.709 0.171 3.5 12/31/09 39,353,159.4 279.6 1,840.02,844.5 269 60.00 3.312 0.151 3.8 12/31/09 37,588,838.4 278.1 1,840.02,676.2 253 60.00 3.093 0.133 3.9 12/31/09 38,972,288.9 279.9 1,840.02,817.0 267 60.00 3.293 0.148 3.9 12/31/09 39,428,898.4 280.3 1,840.02,785.7 267 60.00 3.412 0.152 3.0 12/31/09 40,190,827.9 280.8 1,840.02,861.4 275 60.00 3.420 0.157 3.4 12/31/09 39,185,996.3 280.1 1,840.02,789.9 265 60.00 2.624 0.117 3.5 12/31/09 38,767,892.3 280.3 1,840.02,739.0 262 60.00 3.000 0.131 4.6 12/31/09 38,442,223.1 280.3 1,840.02,674.2 258 60.00 3.156 0.135 4.5 12/31/09 40,332,950.0 282.6 1,840.02,805.8 271 60.00 4.098 0.184 4.5 12/31/09 39,719,207.0 281.4 1,840.02,763.1 267 60.00 4.066 0.179 4.2 12/31/09 40,909,953.3 281.8 1,840.02,823.7 275 60.00 4.043 0.182 3.8 12/31/09 40,074,874.2 281.2 1,840.02,809.6 273 60.00 3.746 0.168 4.8 12/31/09 40,181,452.8 282.2 1,840.02,795.2 273 60.00 3.422 0.153 4.7 12/31/09 40,672,320.4 283.51,840.02,851.5 277 60.00 4.265 0.195 3.8 12/31/09 40,478,284.5 282.4 1,840.02,881.9 276 60.00 4.115 0.189 3.1 12/31/09 36,904,539.3 276.51,840.02,607.4 246 60.00 3.366 0.140 2.8 12/31/09 32,807,185.3 274.51,840.02,228.7 217 60.00 2.860 0.102 2.9 12/31/09 34,976,051.2 274.4 1,840.02,395.1 227 60.00 2.569 0.098 4.2 12/31/09 31,285,671.4 274.7 1,840.02,091.4 205 60.00 2.695 0.090 3.9 12/31/09 36,108,073.5 280.6 1,840.02,511.9 243 60.00 3.717 0.150 3.9 12/31/09 38,152,736.4 280.3 1,840.02,695.6 255 60.00 3.438 0.148 3.6 12/31/09 39,126,325.6 280.2 1,840.02,721.8 262 60.00 3.476 0.152 3.4 12/30/09 38,253,201.3 279.8 1,840.02,744.2 261 60.00 3.157 0.138 3.3 12/30/09 39,020,543.6 280.9 1,840.02,820.5 267 60.00 2.914 0.132 3.5 12/30/09 39,220,684.8 281.7 1,840.02,856.3 270 60.00 2.857 0.130 12/30/09 39,815,720.5 282.3 1,840.02,899.6 276 60.00 3.022 0.140

## Legend: F = Unit Offline E = Exceedance C = Calibration S = Substituted I = Invalid M = Maintenance T = Out of Control * = Suspect

HGOUNCES (OZ) HGT (UG/M3) 

## Time Online Criteria: 1 minute(s)

Edgewater - Unit 4 D4CPFLOW (SCFH)D4DTEMP (DEGF)D4FFACT

(SCF/MBTU)D4HIBAF (MMBTU/HR)D4MEG (MEGAWATT)D4TOLG (MINUTES)HGLB/T (LB/TBTU) 

# Average Data Plant: EDGEWATER Interval: 1 Hour Report Period: 01/01/2009 00:00 Through 12/31/2009 23:59

Source Parameter (Unit)

Total number of Data Points8760 8760 8760 8760 8760 8760 8760 8760 8760