Name: Stephen Ward

Title: Senior Environmental Scientist

Company: Hawaiian Electric Company, Inc.

Sign Date:

Name: Tony Wong

Title: President

Company: AirKinetics Inc.

Sign Date: 8/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Emissions Testing Unit 3

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 10, 2011 Page 1 of 31
Emissions Testing Unit 3

Facility Information:

HI, Kahe

92-200 Farrington Hwy

Kapolei HI 96707

Contact: Stephen Ward

Phone: (808) 543-4535

Fax: (808) 543-4511

Email: stephen.ward@heco.com

Testing Company:

AirKinetics Inc.

1308 S. Allec

Anaheim CA 92805

Contact:Tony Wong

Phone: (714) 245-1945

Fax: (714) 956-2350

Email: wongt@airkineticsinc.com

Air Permit Number:

0240-01-C

Permitted Source ID/Name:

3

Permitted Maximum Process Rate:

892 MMBtu/hr

Max. Normal Operation Process Rate:

732 MMBtu/hr

Target Process Test Rate

723 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1500300501 FRS #: 110000486439

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack 122.5 0 0 122.5 2793 348 2 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack Carbon Monoxide Method 10 3 120 0

stack 2,3,7,8-TCDD Method 23 3 480 0

stack 1,2,3,7,8-PeCDD Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

Thursday, February 10, 2011 Page 2 of 31
Emissions Testing Unit 3

stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

stack OCDD Method 23 3 480 0

stack 2,3,7,8-TCDF Method 23 3 480 0

stack 1,2,3,7,8-PeCDF Method 23 3 480 0

stack 2,3,4,7,8-PeCDF Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

stack OCDF Method 23 3 480 0

stack Other TCDD Method 23 3 480 0

stack Other PeCDD Method 23 3 480 0

stack Other HxCDD Method 23 3 480 0

stack Other HpCDD Method 23 3 480 0

stack Other TCDF Method 23 3 480 0

stack Other PeCDF Method 23 3 480 0

stack Other HxCDF Method 23 3 480 0

stack Other HpCDF Method 23 3 480 0

stack Total Dioxins Method 23 3 480 0

stack Total Furans Method 23 3 480 0

stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

stack Method 23 3 480 0

stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

stack Method 23 3 480 0

stack Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

stack Method 25A 3 120 0

stack Hydrogen Chloride Method 26 3 60 0

stack Hydrogen Fluoride Method 26 3 60 0

stack Total Particulate OTM - 27/28 3 367 0

stack Filterable Particulate OTM - 27/28 3 367 0

Inorganic (Aqueous) 

Condensible Part.

stack OTM - 27/28 3 367 0

Organic Condensible 

Particulate

stack OTM - 27/28 3 367 0

stack Filterable PM2.5 OTM - 27/28 3 367 0

stack Total PM2.5 OTM - 27/28 3 367 0

stack Manganese Method 29 3 240 0

stack Antimony Method 29 3 240 0

stack Arsenic Method 29 3 240 0

stack Beryllium Method 29 3 240 0

stack Cadmium Method 29 3 240 0

Thursday, February 10, 2011 Page 3 of 31
Emissions Testing Unit 3

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

stack Chromium Method 29 3 240 0

stack Lead Method 29 3 240 0

stack Nickel Method 29 3 240 0

stack Selenium Method 29 3 240 0

stack Cobalt Method 29 3 240 0

stack O2 Method 3A O2 3 120 0

stack Co2 Method 3A CO2 3 120 0

stack Filterable Particulate Method 5 3 240 0

stack Sulfur Dioxide Method 6C 3 120 0

stack Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, February 10, 2011 Page 4 of 31
Emissions Testing Unit 3

Sampling / Stack Data Results Summary

Location stack - Method 10

Average

Run Number 1 2 3

Test Date 3/29/2010 3/29/2010 3/29/2010

Run Start Time 8:28:00 AM 11:09:00 

AM

2:02:00 PM

Run Finish Time 10:27:00 AM 1:08:00 PM 4:01:00 PM

Carbon Dioxide, % 11.2 10.9 11.1 11.067

Oxygen, % 5.8 6 5.8 5.867

Dry Volumetric Flow Rate, dry scfm 171397 172855 173128 172,460.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 10.3 10.033

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - Method 23

Average

Run Number 1 2 3

Test Date 3/23/2010 3/24/2010 3/25/2010

Run Start Time 8:20:00 AM 1:20:00 

AM

Run Finish Time 12:20:00 PM 1:00:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 374.793 379.580 372.648 375.674

Moisture Content of Stack Gas, % 10.48 10.14 10.14 10.253

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.4 11.9 11.1 11.467

Oxygen, % 5.9 5.6 6.1 5.867

Average Stack Gas Temperature, °F 249.88 262.46 259.50 257.280

Dry Volumetric Flow Rate, dry scfm 173,073.7 172,666.5 172,111.8 172,617.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 260,368.5 262,480.1 260,564.9 261,137.833

Percent Isokinetic of Sampling Rate, % 100.9 102.5 100.9 101.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 5 of 31
Emissions Testing Unit 3

Location stack - Method 25A

Average

Run Number 1 2 3

Test Date 3/29/2010 3/29/2010 3/29/2010

Run Start Time 8:28:00 AM 11:09:00 

AM

2:02:00 PM

Run Finish Time 10:27:00 AM 1:09:00 PM 4:01:00 PM

Carbon Dioxide, % 11.2 10.9 11.1 11.067

Oxygen, % 5.8 6 5.8 5.867

Dry Volumetric Flow Rate, dry scfm 171397 172855 173128 172,460.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 10.3 10.033

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - Method 26

Average

Run Number 1 2 3

Test Date 3/24/2010 3/24/2010 3/25/2010

Run Start Time 9:22:00 AM 12:25:00 

PM

7:25:00 AM

Run Finish Time 10:22:00 AM 1:25:00 PM 8:50:00 AM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 34.203 34.235 34.703 34.380

Moisture Content of Stack Gas, % 9.57 10.51 11.25 10.443

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.9 11.9 11.1 11.633

Oxygen, % 5.6 5.7 6.1 5.800

Average Stack Gas Temperature, °F 260.00 260.00 260.00 260.000

Dry Volumetric Flow Rate, dry scfm 173,311.6 171,832.9 170,956.2 172,033.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 260,908.7 261,399.8 262,234.6 261,514.367

Percent Isokinetic of Sampling Rate, % 97.5 98.4 100.3 98.733

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 6 of 31
Emissions Testing Unit 3

Location stack - Method 29

Average

Run Number 1 2 3

Test Date 3/26/2010 3/26/2010 3/30/2010

Run Start Time 9:00:00 AM 1:58:00 PM 1:15:00 PM

Run Finish Time 1:28:00 PM 6:03:00 PM 5:42:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 189.261 186.456 186.267 187.328

Moisture Content of Stack Gas, % 9.64 9.71 9.92 9.757

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.9 10.9 11.1 10.967

Oxygen, % 5.9 5.9 5.9 5.900

Average Stack Gas Temperature, °F 260.38 260.42 260.79 260.530

Dry Volumetric Flow Rate, dry scfm 178,233.6 175,005.7 174,018.5 175,752.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 269,748.0 265,082.8 262,578.3 265,803.033

Percent Isokinetic of Sampling Rate, % 99.0 99.3 99.8 99.367

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - Method 5

Average

Run Number 1 2 3

Test Date 3/26/2010 3/26/2010 3/30/2010

Run Start Time 9:00:00 AM 1:58:00 PM 1:15:00 PM

Run Finish Time 1:28:00 PM 6:03:00 PM 5:42:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 189.261 186.456 186.267 187.328

Moisture Content of Stack Gas, % 9.64 9.71 9.92 9.757

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.9 10.8 11.1 10.933

Oxygen, % 5.9 6 5.9 5.933

Average Stack Gas Temperature, °F 260.38 260.42 260.79 260.530

Dry Volumetric Flow Rate, dry scfm 178,233.6 175,038.1 174,018.5 175,763.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 269,748.0 265,131.9 262,578.3 265,819.400

Percent Isokinetic of Sampling Rate, % 99.0 99.3 99.8 99.367

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 7 of 31
Emissions Testing Unit 3

Location stack - Method 6C

Average

Run Number 1 2 3

Test Date 3/24/2010 3/24/2010 3/25/2010

Run Start Time 9:28:00 AM 12:25:00 

PM

7:50:00 AM

Run Finish Time 11:27:00 AM 2:24:00 PM 9:49:00 AM

Carbon Dioxide, % 11.9 11.9 11.9 11.900

Oxygen, % 5.55 5.68 5.61 5.613

Dry Volumetric Flow Rate, dry scfm 172683 172683 172124 172,496.667

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.1 10.1 10.1 10.100

Fuel Type Override Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location stack - Method 7E

Average

Run Number 1 2 3

Test Date 3/24/2010 3/24/2010 3/25/2010

Run Start Time 9:28:00 AM 12:25:00 

PM

7:50:00 AM

Run Finish Time 11:27:00 AM 2:24:00 PM 9:49:00 AM

Carbon Dioxide, % 11.9 11.9 11.9 11.900

Oxygen, % 5.55 5.68 5.61 5.613

Dry Volumetric Flow Rate, dry scfm 172683 172683 172124 172,496.667

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.1 10.1 10.1 10.100

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 8 of 31
Emissions Testing Unit 3

Location stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 3/26/2010 3/30/2010 3/31/2010

Run Start Time 8:00:00 AM 7:42:00 

AM

7:20:00 AM

Run Finish Time 2:23:00 PM 2:12:00 PM 1:40:00 PM

Net Run Time, minutes 368.7460234 367.306872

3

366.7049303

Dry Gas Meter Volume Sampled, dscf 131.416 129.410 130.809 130.545

Moisture Content of Stack Gas, % 9.91 9.78 9.90 9.863

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.9 11.1 11.1 11.033

Oxygen, % 5.9 5.9 5.9 5.900

Average Stack Gas Temperature, °F 260.75 258.08 258.83 259.220

Dry Volumetric Flow Rate, dry scfm 176,963.1 177,269.7 176,423.4 176,885.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 268,765.9 266,065.0 266,310.5 267,047.133

Percent Isokinetic of Sampling Rate, % 87.4 86.2 87.7 87.100

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 9 of 31
Emissions Testing Unit 3

Emissions Summary

Location: stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 1.19E-04 3.83E-04 1.65E-04 0.000

ppm 1.29E-01 4.08E-01 1.78E-01 0.238

ppm@7%O2 1.19E-01 3.81E-01 1.64E-01 0.221

Location: stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000176 0.0000000215 0.0000000163 0.000

lb/mmBtuO2 1.33E-12 1.57E-12 1.25E-12 0.000

ng/dscm 1.66E-03 2.00E-03 1.54E-03 0.002

ng/dscm@7%O2 1.54E-03 1.82E-03 1.45E-03 0.002

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000602 0.00000000765 0.0000000114 0.000

lb/mmBtuO2 4.53E-13 5.58E-13 8.75E-13 0.000

ng/dscm 5.67E-04 7.12E-04 1.08E-03 0.001

ng/dscm@7%O2 5.25E-04 6.47E-04 1.01E-03 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000726 0.00000000923 0.0000000138 0.000

lb/mmBtuO2 5.47E-13 6.73E-13 1.06E-12 0.000

ng/dscm 6.84E-04 8.59E-04 1.31E-03 0.001

ng/dscm@7%O2 6.34E-04 7.80E-04 1.23E-03 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000176 0.0000000165 0.0000000175 0.000

lb/mmBtuO2 1.33E-12 1.20E-12 1.34E-12 0.000

ng/dscm 1.66E-03 1.54E-03 1.66E-03 0.002

ng/dscm@7%O2 1.54E-03 1.40E-03 1.56E-03 0.002

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000526 0.00000000779 0.00000000853 0.000

lb/mmBtuO2 3.96E-13 5.68E-13 6.55E-13 0.000

ng/dscm 4.96E-04 7.25E-04 8.08E-04 0.001

ng/dscm@7%O2 4.60E-04 6.59E-04 7.59E-04 0.001

Compound: 1,2,3,6,7,8-HxCDD

Average

Thursday, February 10, 2011 Page 10 of 31
Emissions Testing Unit 3

RunNumber 1 2 3

Mass_mg 0.0000000164 0.0000000153 0.0000000163 0.000

lb/mmBtuO2 1.24E-12 1.12E-12 1.25E-12 0.000

ng/dscm 1.55E-03 1.42E-03 1.54E-03 0.002

ng/dscm@7%O2 1.44E-03 1.29E-03 1.45E-03 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000494 0.00000000732 0.00000000802 0.000

lb/mmBtuO2 3.72E-13 5.34E-13 6.16E-13 0.000

ng/dscm 4.66E-04 6.81E-04 7.60E-04 0.001

ng/dscm@7%O2 4.32E-04 6.19E-04 7.14E-04 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000016 0.000000015 0.0000000159 0.000

lb/mmBtuO2 1.21E-12 1.09E-12 1.22E-12 0.000

ng/dscm 1.51E-03 1.40E-03 1.51E-03 0.001

ng/dscm@7%O2 1.40E-03 1.27E-03 1.42E-03 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000629 0.00000000933 0.0000000102 0.000

lb/mmBtuO2 4.74E-13 6.80E-13 7.83E-13 0.000

ng/dscm 5.93E-04 8.68E-04 9.67E-04 0.001

ng/dscm@7%O2 5.50E-04 7.89E-04 9.08E-04 0.001

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000964 0.0000000082 0.0000000112 0.000

lb/mmBtuO2 7.26E-13 5.98E-13 8.60E-13 0.000

ng/dscm 9.08E-04 7.63E-04 1.06E-03 0.001

ng/dscm@7%O2 8.41E-04 6.93E-04 9.96E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000134 0.0000000121 0.0000000134 0.000

lb/mmBtuO2 1.01E-12 8.82E-13 1.03E-12 0.000

ng/dscm 1.26E-03 1.13E-03 1.27E-03 0.001

ng/dscm@7%O2 1.17E-03 1.03E-03 1.19E-03 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000178 0.0000000132 0.0000000155 0.000

lb/mmBtuO2 1.34E-12 9.62E-13 1.19E-12 0.000

ng/dscm 1.68E-03 1.23E-03 1.47E-03 0.001

ng/dscm@7%O2 1.56E-03 1.12E-03 1.38E-03 0.001

Thursday, February 10, 2011 Page 11 of 31
Emissions Testing Unit 3

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000071 0.0000000476 0.0000000288 0.000

lb/mmBtuO2 5.35E-12 3.47E-12 2.21E-12 0.000

ng/dscm 6.69E-03 4.43E-03 2.73E-03 0.005

ng/dscm@7%O2 6.20E-03 4.02E-03 2.56E-03 0.004

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000334 0.000000099 0.000000103 0.000

lb/mmBtuO2 2.52E-11 7.22E-12 7.91E-12 0.000

ng/dscm 3.15E-02 9.21E-03 9.76E-03 0.017

ng/dscm@7%O2 2.92E-02 8.37E-03 9.17E-03 0.016

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000212 0.000000025 0.0000000157 0.000

lb/mmBtuO2 1.60E-12 1.82E-12 1.21E-12 0.000

ng/dscm 2.00E-03 2.33E-03 1.49E-03 0.002

ng/dscm@7%O2 1.85E-03 2.12E-03 1.40E-03 0.002

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000467 0.0000000547 0.0000000431 0.000

lb/mmBtuO2 3.52E-12 3.99E-12 3.31E-12 0.000

ng/dscm 4.40E-03 5.09E-03 4.09E-03 0.005

ng/dscm@7%O2 4.08E-03 4.62E-03 3.84E-03 0.004

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.000000806 0.000000247 0.000000238 0.000

lb/mmBtuO2 6.07E-11 1.80E-11 1.83E-11 0.000

ng/dscm 7.60E-02 2.30E-02 2.26E-02 0.041

ng/dscm@7%O2 7.04E-02 2.09E-02 2.12E-02 0.038

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000163 0.0000000521 0.0000000368 0.000

lb/mmBtuO2 1.23E-12 3.80E-12 2.83E-12 0.000

ng/dscm 1.54E-03 4.85E-03 3.49E-03 0.003

ng/dscm@7%O2 1.43E-03 4.41E-03 3.28E-03 0.003

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000535 0.00000000793 0.00000000868 0.000

lb/mmBtuO2 4.03E-13 5.78E-13 6.66E-13 0.000

Thursday, February 10, 2011 Page 12 of 31
Emissions Testing Unit 3

ng/dscm 5.04E-04 7.38E-04 8.23E-04 0.001

ng/dscm@7%O2 4.67E-04 6.70E-04 7.73E-04 0.001

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000138 0.0000000125 0.0000000139 0.000

lb/mmBtuO2 1.04E-12 9.11E-13 1.07E-12 0.000

ng/dscm 1.30E-03 1.16E-03 1.32E-03 0.001

ng/dscm@7%O2 1.20E-03 1.05E-03 1.24E-03 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000007 0.00000000725 0.00000000716 0.000

lb/mmBtuO2 5.27E-13 5.29E-13 5.50E-13 0.000

ng/dscm 6.60E-04 6.75E-04 6.79E-04 0.001

ng/dscm@7%O2 6.12E-04 6.13E-04 6.38E-04 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000129 0.00000000668 0.0000000122 0.000

lb/mmBtuO2 9.72E-13 4.87E-13 9.37E-13 0.000

ng/dscm 1.22E-03 6.22E-04 1.16E-03 0.001

ng/dscm@7%O2 1.13E-03 5.65E-04 1.09E-03 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000269 0.0000000271 0.0000000157 0.000

lb/mmBtuO2 2.03E-12 1.98E-12 1.21E-12 0.000

ng/dscm 2.54E-03 2.52E-03 1.49E-03 0.002

ng/dscm@7%O2 2.35E-03 2.29E-03 1.40E-03 0.002

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000527 0.0000000617 0.0000000442 0.000

lb/mmBtuO2 3.97E-12 4.50E-12 3.39E-12 0.000

ng/dscm 4.97E-03 5.74E-03 4.19E-03 0.005

ng/dscm@7%O2 4.61E-03 5.21E-03 3.94E-03 0.005

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000164 0.000000104 0.0000000492 0.000

lb/mmBtuO2 1.24E-11 7.58E-12 3.78E-12 0.000

ng/dscm 1.55E-02 9.68E-03 4.66E-03 0.010

ng/dscm@7%O2 1.44E-02 8.79E-03 4.38E-03 0.009

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Thursday, February 10, 2011 Page 13 of 31
Emissions Testing Unit 3

Mass_mg 0.0000000371 0.0000000173 0.0000000111 0.000

lb/mmBtuO2 2.79E-12 1.26E-12 8.52E-13 0.000

ng/dscm 3.50E-03 1.61E-03 1.05E-03 0.002

ng/dscm@7%O2 3.24E-03 1.46E-03 9.86E-04 0.002

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000263 0.000000024 0.0000000566 0.000

lb/mmBtuO2 1.98E-12 1.75E-12 4.35E-12 0.000

ng/dscm 2.48E-03 2.23E-03 5.36E-03 0.003

ng/dscm@7%O2 2.30E-03 2.03E-03 5.03E-03 0.003

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000241 0.0000000186 0.0000000278 0.000

lb/mmBtuO2 1.82E-12 1.36E-12 2.13E-12 0.000

ng/dscm 2.27E-03 1.73E-03 2.63E-03 0.002

ng/dscm@7%O2 2.10E-03 1.57E-03 2.47E-03 0.002

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000001 0 0 0.000

lb/mmBtuO2 7.53E-15 0.00E+00 0.00E+00 0.000

ng/dscm 9.42E-06 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 8.73E-06 0.00E+00 0.00E+00 0.000

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Thursday, February 10, 2011 Page 14 of 31
Emissions Testing Unit 3

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0.0000000001 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 7.68E-15 0.000

ng/dscm 0.00E+00 0.00E+00 9.48E-06 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 8.90E-06 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0.00000000001 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 7.68E-16 0.000

ng/dscm 0.00E+00 0.00E+00 9.48E-07 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 8.90E-07 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0 0.00000013932 0 0.000

lb/mmBtuO2 0.00E+00 1.02E-11 0.00E+00 0.000

ng/dscm 0.00E+00 1.30E-02 0.00E+00 0.004

ng/dscm@7%O2 0.00E+00 1.18E-02 0.00E+00 0.004

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.000000071 0.000000076 0.000000108 0.000

lb/mmBtuO2 5.35E-12 5.54E-12 8.29E-12 0.000

ng/dscm 6.69E-03 7.07E-03 1.02E-02 0.008

ng/dscm@7%O2 6.20E-03 6.42E-03 9.58E-03 0.007

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.000000068 0.000000196 0.000000075 0.000

lb/mmBtuO2 5.12E-12 1.43E-11 5.76E-12 0.000

ng/dscm 6.41E-03 1.82E-02 7.11E-03 0.011

ng/dscm@7%O2 5.94E-03 1.65E-02 6.68E-03 0.010

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0.00000002822 0.00000002722 0.00000003061 0.000

lb/mmBtuO2 2.13E-12 1.98E-12 2.35E-12 0.000

Thursday, February 10, 2011 Page 15 of 31
Emissions Testing Unit 3

ng/dscm 2.66E-03 2.53E-03 2.90E-03 0.003

ng/dscm@7%O2 2.46E-03 2.30E-03 2.72E-03 0.002

Location: stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 5.00E-04 3.80E-04 3.29E-04 0.000

ppm 3.43E-01 2.57E-01 2.26E-01 0.275

ppm@7%O2 3.16E-01 2.40E-01 2.08E-01 0.255

Location: stack - Method 26

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.269 0.306 0.315 0.297

lb/mmBtuO2 2.18E-04 2.49E-04 2.60E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.154 0.162 0.155 0.157

lb/mmBtuO2 1.25E-04 1.32E-04 1.28E-04 0.000

Location: stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.004706 0.003925 0.007279 0.005

lb/mmBtuO2 7.02E-07 5.94E-07 1.10E-06 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.02918 0.02863 0.03332 0.030

lb/mmBtuO2 4.35E-06 4.33E-06 5.05E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00056 0.00055 0.00057 0.001

lb/mmBtuO2 8.35E-08 8.33E-08 8.64E-08 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.000925 0.000875 0.000608 0.001

lb/mmBtuO2 1.38E-07 1.32E-07 9.21E-08 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Thursday, February 10, 2011 Page 16 of 31
Emissions Testing Unit 3

Mass_mg 0.02612 0.0141 0.0243 0.022

lb/mmBtuO2 3.90E-06 2.13E-06 3.68E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.246904 0.242958 0.260949 0.250

lb/mmBtuO2 3.68E-05 3.68E-05 3.95E-05 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.011 0.00995 0.00927 0.010

lb/mmBtuO2 1.64E-06 1.51E-06 1.40E-06 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.05004 0.04324 0.04451 0.046

lb/mmBtuO2 7.46E-06 6.55E-06 6.75E-06 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 3.94942 3.92294 4.26064 4.044

lb/mmBtuO2 5.89E-04 5.94E-04 6.46E-04 0.001

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.015248 0.016055 0.018905 0.017

lb/mmBtuO2 2.27E-06 2.43E-06 2.87E-06 0.000

Location: stack - Method 5

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 126.5 107.6 158.7 130.933

lb/mmBtuO2 1.89E-02 1.64E-02 2.41E-02 0.020

Location: stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 3.81E-01 4.01E-01 3.99E-01 0.394

ppm 1.83E+02 1.91E+02 1.91E+02 188.333

ppm@7%O2 1.66E+02 1.74E+02 1.74E+02 171.333

Location: stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

Thursday, February 10, 2011 Page 17 of 31
Emissions Testing Unit 3

Process Run Data

lb/mmBtuO2 3.94E-01 3.97E-01 3.92E-01 0.394

ppm 2.64E+02 2.63E+02 2.61E+02 262.667

ppm@7%O2 2.39E+02 2.40E+02 2.37E+02 238.667

Location: stack - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 110.4 129.1 105.9 115.133

lb/mmBtuO2 2.37E-02 2.82E-02 2.29E-02 0.025

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 59.2 87.8 66.9 71.300

lb/mmBtuO2 1.27E-02 1.92E-02 1.44E-02 0.015

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 4.8 6.3 4.7 5.267

lb/mmBtuO2 1.03E-03 1.37E-03 1.01E-03 0.001

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 4.6 6.9 10 7.167

lb/mmBtuO2 9.88E-04 1.51E-03 2.16E-03 0.002

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 117.8 140.3 118.6 125.567

lb/mmBtuO2 2.53E-02 3.06E-02 2.56E-02 0.027

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 66.6 99 79.6 81.733

lb/mmBtuO2 1.43E-02 2.16E-02 1.72E-02 0.018

Thursday, February 10, 2011 Page 18 of 31
Emissions Testing Unit 3

Process Run Data

Run Name Value UOM Comments

Target

Value

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

1 0

1 Unit Gross Electric Generation 80.38 Mwe

1 Unit Net Electric Generation 76.88 MWh

1 Steam Output 541.8 1,000 lbs steam/hr

1 Average Heat Input 737.45 MMBtu/hr EPA Method 23: 

K3-m23-1

1 Fuel Oil Firing Rate 38.67 Klb/hr March 23, 2010 

Test Day

3 0

3 0

3 0

3 0

3 0

3 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

3 0

3 Unit Gross Electric Generation 80.59 Mwe

3 Unit Net Electric Generation 77.1 MWh EPA Method 

26/CTM-033: K3-

M26-1, K3-M26-

2, K3-M26-3

3 Steam Output 543.2 1,000 lbs steam/hr EPA Method 23: 

K3-M23-2

Thursday, February 10, 2011 Page 19 of 31
Emissions Testing Unit 3

3 Average Heat Input 730.98 MMBtu/hr EPA Method 3A, 

6C and 7E: Run 1 

and Run 2

3 Fuel Oil Firing Rate 38.43 Klb/hr March 24, 2010 

Test Day

4 0

4 0

4 0

4 0

4 0

4 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

4 0

4 Unit Gross Electric Generation 80.3 Mwe

4 Unit Net Electric Generation 76.8 MWh

4 Steam Output 541.2 1,000 lbs steam/hr EPA Method 23: 

K3-M23-3

4 Average Heat Input 732.50 MMBtu/hr EPA Method 3A, 

6C, and 7E: Run 3

4 Fuel Oil Firing Rate 38.37 Klb/hr March 25, 2010 

Test Day

5 0

5 0

5 0

5 0

5 0

5 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

5 0

5 Unit Gross Electric Generation 80.1 Mwe

5 Unit Net Electric Generation 76.71 MWh

5 Steam Output 540.7 1,000 lbs steam/hr EPA Method 

OTM 27/28: K3-

OTM27/28-1

5 Average Heat Input 730.36 MMBtu/hr EPA Method 5/29: 

K3-M5/29-1, K3-

M5/29-2

5 Fuel Oil Firing Rate 38.38 Klb/hr March 26, 2010 

Test Day

6 0

6 0

6 0

Thursday, February 10, 2011 Page 20 of 31
Emissions Testing Unit 3

6 0

6 0

6 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

6 0 EPA Method 

0031/SW-846 

8260B: K3-

M0031-1, K3-

M0031-2, K3-

M0031-3

6 Unit Gross Electric Generation 79.87 Mwe EPA Method 

0010/SW-846 

8270D: K3-

M0010-1, K3-

M0010-2, K3-

M0010-3

6 Unit Net Electric Generation 76.33 MWh EPA Method 316: 

K3-M316-1, K3-

M316-2, K3-

M316-3

6 Steam Output 538.7 1,000 lbs steam/hr EPA Method 10 

and 25A: Run 1, 

Run 2, Run 3

6 Average Heat Input 735.78 MMBtu/hr EPA Method 18: 

K3-M18-1, K3-

M18-2, K3-M18-3

6 Fuel Oil Firing Rate 38.18 Klb/hr March 29, 2010 

Test Day

7 0

7 0

7 0

7 0

7 0

7 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

7 0

7 Unit Gross Electric Generation 80.18 Mwe

7 Unit Net Electric Generation 76.71 MWh EPA Method 

OTM 27/28: K3-

OTM27/28-2

7 Steam Output 540.8 1,000 lbs steam/hr EPA Method 30B: 

K3-M30B-1, K3-

M30B-2

7 Average Heat Input 728.95 MMBtu/hr EPA Method 5/29: 

K3-M5/29-3

7 Fuel Oil Firing Rate 38.14 Klb/hr March 30, 2010 

Test Day

Thursday, February 10, 2011 Page 21 of 31
Emissions Testing Unit 3

APCD Run Data

Process Lab Run Data

8 0

8 0

8 0

8 0

8 0

8 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

8 0

8 Unit Gross Electric Generation 79.76 Mwe

8 Unit Net Electric Generation 76.33 MWh

8 Steam Output 538.3 1,000 lbs steam/hr EPA Method: K3-

OTM27/28-3

8 Average Heat Input 727.97 MMBtu/hr EPA Method: K3-

M30B-3

8 Fuel Oil Firing Rate 38.29 Klb/hr March 31, 2010 

Test Day

Run Name Value UOM Comments

Target

Value

1 None 0

1 0

1 0

1 0

Run Name Value UOM Comments

1 none 0

1 0

1 0

1 0

1 0

Thursday, February 10, 2011 Page 22 of 31
Emissions Testing Unit 3

Sampling / Stack Data Results Detail

Location stack - Method 10

Average

Run Number 1 2 3

Test Date 3/29/2010 3/29/2010 3/29/2010

Run Start Time 8:28:00 AM 11:09:00 AM 2:02:00 PM

Run Finish Time 10:27:00 AM 1:08:00 PM 4:01:00 PM

Carbon Dioxide, % 11.2 10.9 11.1 11.067

Oxygen, % 5.8 6 5.8 5.867

Fuel Factor 1.35 1.37 1.36

Dry Volumetric Flow Rate, dry scfm 171397 172855 173128 172,460.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 10.3 10.033

Analyzer Make Thermo 

Electron

Thermo 

Electron

Thermo 

Electron

Analyzer Model 48 48 48 48.000

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 0 0 0 0.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response -0.02 -0.04 0.06 0.000

Calibration Pre Zero Cylinder Bias -0.5 -0.61 -0.06 -0.390

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID COCC149350-

Diluted2

COCC149350-

Diluted2

COCC149350-

Diluted2

Calibration Pre High Cylinder Instrument Response 9.19 9.03 9.22 9.147

Calibration Pre High Cylinder Bias 0.06 -0.83 0.22 -0.183

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response -0.04 0.06 0 0.007

Calibration Post Zero Cylinder Bias -0.61 -0.06 -0.39 -0.353

Calibration Post Zero Cylinder Drift 0.11 0.55 0.33 0.330

Calibration Post High Cylinder ID COCC149350-

Diluted2

COCC149350-

Diluted2

COCC149350-

Diluted2

Calibration Post High Cylinder Instrument Response 9.03 9.22 9.16 9.137

Calibration Post High Cylinder Bias -0.83 0.22 -0.11 -0.240

Calibration Post High Cylinder Drift 0.89 1.05 0.33 0.757

Cavg 0.1 0.42 0.21 0.243

Cavg Units ppmvd ppmvd ppmvd

Cgas 0.1291 0.4084 0.1784 0.239

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 10, 2011 Page 23 of 31
Emissions Testing Unit 3

Location stack - Method 23

Average

Run Number 1 2 3

Test Date 3/23/2010 3/24/2010 3/25/2010

Run Start Time 8:20:00 AM 1:20:00 AM

Run Finish Time 12:20:00 PM 1:00:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.259 0.259 0.259 0.259

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.96 0.96 0.96 0.960

Barometric Pressure, inches of Mercury 29.9 30 30 29.967

Average Orifice Meter Differential, inches H2O 2.22 2.23 2.19 2.213

Dry Gas Meter Volume Sampled, cubic feet 421.922 426.627 418.089 422.213

Average Dry Gas Meter Temperature, °F 113.35 114.35 113.27 113.657

Dry Gas Meter Volume Sampled, dscf 374.793 379.580 372.648 375.674

Total Moisture Liquid collected, g 932.5 910.3 893.6 912.133

Volume of Water Vapor, standard cubic feet 43.89 42.85 42.06 42.933

Moisture Content of Stack Gas, % 10.48 10.14 10.14 10.253

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8952 0.8986 0.8986 0.897

Carbon Dioxide, % 11.4 11.9 11.1 11.467

Oxygen, % 5.9 5.6 6.1 5.867

Carbon Monoxide & Nitrogen, % 82.7 82.5 82.8 82.667

Fuel Factor 1.32 1.29 1.33

Dry Molecular Weight, lb/lb-Mole 30.06 30.13 30.02 30.070

Wet Molecular weight, lb/lb-Mole 28.80 28.90 28.80 28.833

Flue Gas Static Pressure, inches of H2O -0.38 -0.4 -0.38 -0.387

Absolute Flue Gas Pressure, inches of Mercury 29.87 29.97 29.97 29.937

Average Stack Gas Temperature, °F 249.88 262.46 259.50 257.280

Average Velocity Head, inches of H2O 0.6606888225

97478

0.664144461

797009

0.654939322

371533

0.660

Average Stack Gas Velocity, feet/second 53.02 53.45 53.06 53.177

Stack Cross-Sectional Area, square feet 81.846 81.846 81.846 81.846

Dry Volumetric Flow Rate, dry scfm 173,073.7 172,666.5 172,111.8 172,617.333

Actual Wet Volumetric Flue Gas Flow Rate, acfm 260,368.5 262,480.1 260,564.9 261,137.833

Percent Isokinetic of Sampling Rate, % 100.9 102.5 100.9 101.433

Percent Excess Air, % 37.0 34.6 38.7 36.767

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 122.5 122.5 122.5

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 24 of 31
Emissions Testing Unit 3

Location stack - Method 25A

Average

Run Number 1 2 3

Test Date 3/29/2010 3/29/2010 3/29/2010

Run Start Time 8:28:00 AM 11:09:00 AM 2:02:00 PM

Run Finish Time 10:27:00 AM 1:09:00 PM 4:01:00 PM

Carbon Dioxide, % 11.2 10.9 11.1 11.067

Oxygen, % 5.8 6 5.8 5.867

Fuel Factor 1.35 1.37 1.36

Dry Volumetric Flow Rate, dry scfm 171397 172855 173128 172,460.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 9.9 9.9 10.3 10.033

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0.06 0.02 0.07 0.050

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

Calibration Pre High Cylinder Instrument Response 2.48 2.51 2.49 2.493

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0.02 0.07 0.04 0.043

Calibration Post Zero Cylinder Bias -0.53 0.66 -0.4 -0.090

Calibration Post Zero Cylinder Drift 0.53 0.66 0.4 0.530

Calibration Post High Cylinder ID THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

THC-CC163385-

Diluted3

Calibration Post High Cylinder Instrument Response 2.51 2.49 2.49 2.497

Calibration Post High Cylinder Bias 0.4 -0.26 0 0.047

Calibration Post High Cylinder Drift 0.4 0.26 0 0.220

Cavg 0.34 0.27 0.25 0.287

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.3431 0.2574 0.2259 0.275

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0.3091649694

50102

0.231873727

087576

0.202607802

874743

0.248

Cgasw Units ppmvw ppmvw ppmvw

Thursday, February 10, 2011 Page 25 of 31
Emissions Testing Unit 3

Location stack - Method 26

Average

Run Number 1 2 3

Test Date 3/24/2010 3/24/2010 3/25/2010

Run Start Time 9:22:00 AM 12:25:00 PM 7:25:00 AM

Run Finish Time 10:22:00 AM 1:25:00 PM 8:50:00 AM

Net Traversing Points 12 12 12

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches 0.225 0.225 0.225 0.225

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 1.03 1.03 1.030

Barometric Pressure, inches of Mercury 30 30 30 30.000

Average Orifice Meter Differential, inches H2O 1.20 1.20 1.20 1.200

Dry Gas Meter Volume Sampled, cubic feet 35.528 35.749 36.019 35.765

Average Dry Gas Meter Temperature, °F 108.08 111.08 107.63 108.930

Dry Gas Meter Volume Sampled, dscf 34.203 34.235 34.703 34.380

Total Moisture Liquid collected, g 77 85.5 93.5 85.333

Volume of Water Vapor, standard cubic feet 3.62 4.02 4.40 4.013

Moisture Content of Stack Gas, % 9.57 10.51 11.25 10.443

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9043 0.8949 0.8875 0.896

Carbon Dioxide, % 11.9 11.9 11.1 11.633

Oxygen, % 5.6 5.7 6.1 5.800

Carbon Monoxide & Nitrogen, % 82.5 82.4 82.8 82.567

Fuel Factor 1.29 1.28 1.33

Dry Molecular Weight, lb/lb-Mole 30.13 30.13 30.02 30.093

Wet Molecular weight, lb/lb-Mole 28.97 28.86 28.67 28.833

Flue Gas Static Pressure, inches of H2O -0.4 -0.4 -0.38 -0.393

Absolute Flue Gas Pressure, inches of Mercury 29.97 29.97 29.97 29.970

Average Stack Gas Temperature, °F 260.00 260.00 260.00 260.000

Average Velocity Head, inches of H2O 0.66 0.66 0.66 0.660

Average Stack Gas Velocity, feet/second 53.13 53.23 53.40 53.253

Stack Cross-Sectional Area, square feet 81.846 81.846 81.846 81.846

Dry Volumetric Flow Rate, dry scfm 173,311.6 171,832.9 170,956.2 172,033.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 260,908.7 261,399.8 262,234.6 261,514.367

Percent Isokinetic of Sampling Rate, % 97.5 98.4 100.3 98.733

Percent Excess Air, % 34.6 35.5 38.7 36.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 122.5 122.5 122.5

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 26 of 31
Emissions Testing Unit 3

Location stack - Method 29

Average

Run Number 1 2 3

Test Date 3/26/2010 3/26/2010 3/30/2010

Run Start Time 9:00:00 AM 1:58:00 PM 1:15:00 PM

Run Finish Time 1:28:00 PM 6:03:00 PM 5:42:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.259 0.259 0.259 0.259

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 1.03 0.96 1.007

Barometric Pressure, inches of Mercury 29.9 29.9 30.1 29.967

Average Orifice Meter Differential, inches H2O 2.26 2.17 2.16 2.197

Dry Gas Meter Volume Sampled, cubic feet 198.432 196.087 209.079 201.199

Average Dry Gas Meter Temperature, °F 112.98 114.60 115.40 114.327

Dry Gas Meter Volume Sampled, dscf 189.261 186.456 186.267 187.328

Total Moisture Liquid collected, g 428.9 426.2 436 430.367

Volume of Water Vapor, standard cubic feet 20.19 20.06 20.52 20.257

Moisture Content of Stack Gas, % 9.64 9.71 9.92 9.757

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9036 0.9029 0.9008 0.902

Carbon Dioxide, % 10.9 10.9 11.1 10.967

Oxygen, % 5.9 5.9 5.9 5.900

Carbon Monoxide & Nitrogen, % 83.2 83.2 83 83.133

Fuel Factor 1.38 1.38 1.35

Dry Molecular Weight, lb/lb-Mole 29.98 29.98 30.01 29.990

Wet Molecular weight, lb/lb-Mole 28.83 28.82 28.82 28.823

Flue Gas Static Pressure, inches of H2O -0.65 -0.65 -0.66 -0.653

Absolute Flue Gas Pressure, inches of Mercury 29.85 29.85 30.05 29.917

Average Stack Gas Temperature, °F 260.38 260.42 260.79 260.530

Average Velocity Head, inches of H2O 0.6990591236

49447

0.674695230

253036

0.666223628

750813

0.680

Average Stack Gas Velocity, feet/second 54.93 53.98 53.47 54.127

Stack Cross-Sectional Area, square feet 81.846 81.846 81.846 81.846

Dry Volumetric Flow Rate, dry scfm 178,233.6 175,005.7 174,018.5 175,752.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 269,748.0 265,082.8 262,578.3 265,803.033

Percent Isokinetic of Sampling Rate, % 99.0 99.3 99.8 99.367

Percent Excess Air, % 36.7 36.7 36.8 36.733

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 122.5 122.5 122.5

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 27 of 31
Emissions Testing Unit 3

Location stack - Method 5

Average

Run Number 1 2 3

Test Date 3/26/2010 3/26/2010 3/30/2010

Run Start Time 9:00:00 AM 1:58:00 PM 1:15:00 PM

Run Finish Time 1:28:00 PM 6:03:00 PM 5:42:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.259 0.259 0.259 0.259

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 1.03 0.96 1.007

Barometric Pressure, inches of Mercury 29.9 29.9 30.1 29.967

Average Orifice Meter Differential, inches H2O 2.26 2.17 2.16 2.197

Dry Gas Meter Volume Sampled, cubic feet 198.432 196.087 209.079 201.199

Average Dry Gas Meter Temperature, °F 112.98 114.60 115.40 114.327

Dry Gas Meter Volume Sampled, dscf 189.261 186.456 186.267 187.328

Total Moisture Liquid collected, g 428.9 426.2 436 430.367

Volume of Water Vapor, standard cubic feet 20.19 20.06 20.52 20.257

Moisture Content of Stack Gas, % 9.64 9.71 9.92 9.757

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9036 0.9029 0.9008 0.902

Carbon Dioxide, % 10.9 10.8 11.1 10.933

Oxygen, % 5.9 6 5.9 5.933

Carbon Monoxide & Nitrogen, % 83.2 83.2 83 83.133

Fuel Factor 1.38 1.38 1.35

Dry Molecular Weight, lb/lb-Mole 29.98 29.97 30.01 29.987

Wet Molecular weight, lb/lb-Mole 28.83 28.81 28.82 28.820

Flue Gas Static Pressure, inches of H2O -0.65 -0.65 -0.66 -0.653

Absolute Flue Gas Pressure, inches of Mercury 29.85 29.85 30.05 29.917

Average Stack Gas Temperature, °F 260.38 260.42 260.79 260.530

Average Velocity Head, inches of H2O 0.6990591236

49447

0.674695230

253036

0.666223628

750813

0.680

Average Stack Gas Velocity, feet/second 54.93 53.99 53.47 54.130

Stack Cross-Sectional Area, square feet 81.846 81.846 81.846 81.846

Dry Volumetric Flow Rate, dry scfm 178,233.6 175,038.1 174,018.5 175,763.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 269,748.0 265,131.9 262,578.3 265,819.400

Percent Isokinetic of Sampling Rate, % 99.0 99.3 99.8 99.367

Percent Excess Air, % 36.7 37.6 36.8 37.033

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 122.5 122.5 122.5

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 28 of 31
Emissions Testing Unit 3

Location stack - Method 6C

Average

Run Number 1 2 3

Test Date 3/24/2010 3/24/2010 3/25/2010

Run Start Time 9:28:00 AM 12:25:00 PM 7:50:00 AM

Run Finish Time 11:27:00 AM 2:24:00 PM 9:49:00 AM

Carbon Dioxide, % 11.9 11.9 11.9 11.900

Oxygen, % 5.55 5.68 5.61 5.613

Fuel Factor 1.29 0 1.28

Dry Volumetric Flow Rate, dry scfm 172683 172683 172124 172,496.667

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.1 10.1 10.1 10.100

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias -49.64 0 0 -16.547

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

Calibration Pre High Cylinder Instrument Response 453.07 451 454 452.690

Calibration Pre High Cylinder Bias -50.65 -0.51 -0.18 -17.113

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0 0 1 0.333

Calibration Post Zero Cylinder Bias -49.64 0 0.11 -16.510

Calibration Post Zero Cylinder Drift 0 0 0.11 0.037

Calibration Post High Cylinder ID SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

SO2-CC102092-

Diluted1

Calibration Post High Cylinder Instrument Response 451 452.47 453.84 452.437

Calibration Post High Cylinder Bias -0.51 -0.35 -0.2 -0.353

Calibration Post High Cylinder Drift 50.14 0.16 0.02 16.773

Cavg 180.19 188.29 189.09 185.857

Cavg Units ppmvd ppmvd ppmvd

Cgas 182.9664 191.3182 190.9109 188.399

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 10, 2011 Page 29 of 31
Emissions Testing Unit 3

Location stack - Method 7E

Average

Run Number 1 2 3

Test Date 3/24/2010 3/24/2010 3/25/2010

Run Start Time 9:28:00 AM 12:25:00 PM 7:50:00 AM

Run Finish Time 11:27:00 AM 2:24:00 PM 9:49:00 AM

Carbon Dioxide, % 11.9 11.9 11.9 11.900

Oxygen, % 5.55 5.68 5.61 5.613

Fuel Factor 1.29 1.28 1.28

Dry Volumetric Flow Rate, dry scfm 172683 172683 172124 172,496.667

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 10.1 10.1 10.1 10.100

Analyzer Make CAI Model CAI Model CAI Model

Analyzer Model 600 600 600 600.000

Analyzer Serial Number

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 4 4 4 4.000

Calibration Pre Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

Calibration Pre High Cylinder Instrument Response 457.27 451.8 455.47 454.847

Calibration Pre High Cylinder Bias 0.25 -0.13 -0.32 -0.067

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Nitrogen Nitrogen Nitrogen

Calibration Post Zero Cylinder Instrument Response 0 0.33 0 0.110

Calibration Post Zero Cylinder Bias 0 0.04 0 0.013

Calibration Post Zero Cylinder Drift 0 0.04 0 0.013

Calibration Post High Cylinder ID NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

NOx-CC187760-

Diluted1

Calibration Post High Cylinder Instrument Response 451.8 456.27 454.53 454.200

Calibration Post High Cylinder Bias -0.35 0.36 -0.42 -0.137

Calibration Post High Cylinder Drift 0.6 0.49 0.1 0.397

Cavg 262.07 261.28 259.53 260.960

Cavg Units ppmvd ppmvd ppmvd

Cgas 264.0678 263.491 261.2412 262.933

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Oil Oil Oil

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, February 10, 2011 Page 30 of 31
Emissions Testing Unit 3

Location stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 3/26/2010 3/30/2010 3/31/2010

Run Start Time 8:00:00 AM 7:42:00 AM 7:20:00 AM

Run Finish Time 2:23:00 PM 2:12:00 PM 1:40:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 368.7460234 367.3068723 366.7049303

Nozzle Diameter, inches 0.186 0.186 0.186 0.186

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.96 1.03 0.96 0.983

Barometric Pressure, inches of Mercury 29.9 30.1 30 30.000

Average Orifice Meter Differential, inches H2O 0.47 0.44 0.43 0.447

Dry Gas Meter Volume Sampled, cubic feet 147.569 134.670 145.942 142.727

Average Dry Gas Meter Temperature, °F 109.46 109.96 107.63 109.017

Dry Gas Meter Volume Sampled, dscf 131.416 129.410 130.809 130.545

Total Moisture Liquid collected, g 307 298 305.5 303.500

Volume of Water Vapor, standard cubic feet 14.45 14.03 14.38 14.287

Moisture Content of Stack Gas, % 9.91 9.78 9.90 9.863

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9009 0.9022 0.901 0.901

Carbon Dioxide, % 10.9 11.1 11.1 11.033

Oxygen, % 5.9 5.9 5.9 5.900

Carbon Monoxide & Nitrogen, % 83.2 83 83 83.067

Fuel Factor 1.38 1.35 1.35

Dry Molecular Weight, lb/lb-Mole 29.98 30.01 30.01 30.000

Wet Molecular weight, lb/lb-Mole 28.79 28.84 28.82 28.817

Flue Gas Static Pressure, inches of H2O -0.65 -0.66 -0.65 -0.653

Absolute Flue Gas Pressure, inches of Mercury 29.85 30.05 29.95 29.950

Average Stack Gas Temperature, °F 260.75 258.08 258.83 259.220

Average Velocity Head, inches of H2O 0.6924582996

83992

0.687063760

57363

0.684813687

307511

0.688

Average Stack Gas Velocity, feet/second 54.73 54.18 54.23 54.380

Stack Cross-Sectional Area, square feet 81.846 81.846 81.846 81.846

Dry Volumetric Flow Rate, dry scfm 176,963.1 177,269.7 176,423.4 176,885.400

Actual Wet Volumetric Flue Gas Flow Rate, acfm 268,765.9 266,065.0 266,310.5 267,047.133

Percent Isokinetic of Sampling Rate, % 87.4 86.2 87.7 87.100

Percent Excess Air, % 36.7 36.8 36.8 36.767

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 122.5 122.5 122.5

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 31 of 31