Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, January 14, 2011 Page 1 of 20
Facility Information:

AES Puerto Rico

CARRETERA #3 KM 142

GUAYAMA PR 00784

Contact: William G. Vela

Phone: 787-866-8117

Fax:

Email:

Testing Company:

URS Corporation

1600 Perimeter Park Drive, Suite 400

Morrisville NC 27560

Contact:Brad Justus

Phone: 919-461-1326

Fax: 919-461-1415

Email: brad_justus@urscorp.com

Air Permit Number:

68029

Permitted Source ID/Name:

Unit 1

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

*******

Industry/SCC/NAIS 221122

Sampling Location Information:

Test Parameter Information:

AFS #: 7205700056 FRS #:

SCC / Description 10100218 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Atmospheric Fluidized Bed Combustion: Circulating Bed (Bitum. Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 192 0 0 0 2304 2688 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Friday, January 14, 2011 Page 2 of 20
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Cobalt Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Friday, January 14, 2011 Page 3 of 20
Sampling / Stack Data Results Summary

Location Stack Exit - Method 25A

Average

Run Number 1 2 3

Test Date 3/12/2010 3/12/2010 3/12/2010

Run Start Time

Run Finish Time

Carbon Dioxide, % 12.5 12.3 12.7 12.500

Oxygen, % 6 6.8 6.1 6.300

Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13 13.1 12.8 12.967

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 3/3/2010 3/4/2010 3/4/2010

Run Start Time 1:30:00 PM 9:07:00 

AM

1:45:00 PM

Run Finish Time 6:09:00 PM 12:41:00 

PM

5:25:00 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 100.589 100.725 100.389 100.568

Moisture Content of Stack Gas, % 13.81 14.03 13.94 13.927

Moisture Saturation at Stack Gas Temperature, % 49.22 50.08 49.64 49.647

Carbon Dioxide, % 12.4 13.4 11.4 12.400

Oxygen, % 6 5 7.4 6.133

Average Stack Gas Temperature, °F 178.11 178.75 178.36 178.407

Dry Volumetric Flow Rate, dry scfm 560,550.8 568,588.9 567,064.9 565,401.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 791,018.1 807,666.1 804,167.6 800,950.600

Percent Isokinetic of Sampling Rate, % 98.7 97.4 97.3 97.800

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 14, 2011 Page 4 of 20
Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 7/29/2010 7/29/2010 7/30/2010

Run Start Time 8:25:00 AM 4:20:00 PM 11:00:00 AM

Run Finish Time 12:48:00 PM 10:32:00 

PM

3:18:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 144.452 145.707 144.751 144.970

Moisture Content of Stack Gas, % 13.99 14.73 13.61 14.110

Moisture Saturation at Stack Gas Temperature, % 55.61 55.48 56.94 56.010

Carbon Dioxide, % 11.7 12.1 12.2 12.000

Oxygen, % 6.3 6.5 6.4 6.400

Average Stack Gas Temperature, °F 183.96 183.85 184.96 184.257

Dry Volumetric Flow Rate, dry scfm 603,450.4 598,867.4 600,841.2 601,053.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 854,835.2 855,559.0 850,130.3 853,508.167

Percent Isokinetic of Sampling Rate, % 98.7 100.3 99.3 99.433

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 4

Test Date 7/29/2010 7/29/2010 7/31/2010

Run Start Time 12:09:36 AM 3:15:00 PM 9:00:00 AM

Run Finish Time 1:58:54 PM 9:49:09 PM 3:28:09 PM

Net Run Time, minutes 366.67 370.35 363

Dry Gas Meter Volume Sampled, dscf 119.573 121.145 117.099 119.272

Moisture Content of Stack Gas, % 14.02 14.08 14.16 14.087

Moisture Saturation at Stack Gas Temperature, % 57.41 56.27 52.39 55.357

Carbon Dioxide, % 11.7 12.1 12.5 12.100

Oxygen, % 6.3 6.5 6.4 6.400

Average Stack Gas Temperature, °F 185.42 184.50 181.08 183.667

Dry Volumetric Flow Rate, dry scfm 625,913.0 623,054.1 616,861.5 621,942.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 888,975.5 884,270.7 874,861.0 882,702.400

Percent Isokinetic of Sampling Rate, % 103.8 104.6 104.2 104.200

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 14, 2011 Page 5 of 20
Emissions Summary

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 4.95E-04 2.49E-03 1.66E-03 0.002

ppm 3.15E-01 1.50E+00 1.05E+00 0.955

ppm@7%O2 2.94E-01 1.48E+00 9.86E-01 0.920

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.375 0.313 0.315 0.334

Elb/hr 2.76E-01 2.34E-01 2.35E-01 0.248

lb/mmBtuO2 1.13E-04 8.81E-05 1.05E-04 0.000

mg/dscm 1.32E-01 1.10E-01 1.11E-01 0.118

mg/dscm@7%O2 1.23E-01 9.62E-02 1.14E-01 0.111

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.384 0.32 0.307 0.337

Elb/hr 2.83E-01 2.39E-01 2.29E-01 0.250

lb/mmBtuO2 1.15E-04 9.00E-05 1.02E-04 0.000

mg/dscm 1.35E-01 1.12E-01 1.08E-01 0.118

mg/dscm@7%O2 1.26E-01 9.79E-02 1.11E-01 0.112

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.00151 0.00221 0.00111 0.002

Elb/hr 8.34E-04 1.20E-03 6.09E-04 0.001

lb/mmBtuO2 3.23E-07 4.75E-07 2.38E-07 0.000

mg/dscm 3.69E-04 5.36E-04 2.71E-04 0.000

mg/dscm@7%O2 3.51E-04 5.17E-04 2.60E-04 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.00299 0.00468 0.00209 0.003

Elb/hr 1.65E-03 2.54E-03 1.15E-03 0.002

lb/mmBtuO2 6.39E-07 1.01E-06 4.49E-07 0.000

mg/dscm 7.31E-04 1.13E-03 5.10E-04 0.001

mg/dscm@7%O2 6.96E-04 1.09E-03 4.89E-04 0.001

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00038 0.00055 0.00029 0.000

Friday, January 14, 2011 Page 6 of 20
Elb/hr 2.10E-04 2.99E-04 1.59E-04 0.000

lb/mmBtuO2 8.12E-08 1.18E-07 6.23E-08 0.000

mg/dscm 9.29E-05 1.33E-04 7.08E-05 0.000

mg/dscm@7%O2 8.84E-05 1.28E-04 6.79E-05 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00029 0.00035 0.00127 0.001

Elb/hr 1.60E-04 1.90E-04 6.97E-04 0.000

lb/mmBtuO2 6.20E-08 7.52E-08 2.73E-07 0.000

mg/dscm 7.09E-05 8.48E-05 3.10E-04 0.000

mg/dscm@7%O2 6.75E-05 8.19E-05 2.97E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.00831 0.01041 0.00642 0.008

Elb/hr 4.59E-03 5.66E-03 3.52E-03 0.005

lb/mmBtuO2 1.78E-06 2.24E-06 1.38E-06 0.000

mg/dscm 2.03E-03 2.52E-03 1.57E-03 0.002

mg/dscm@7%O2 1.93E-03 2.43E-03 1.51E-03 0.002

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00335 0.00514 0.00264 0.004

Elb/hr 1.85E-03 2.79E-03 1.45E-03 0.002

lb/mmBtuO2 7.16E-07 1.10E-06 5.67E-07 0.000

mg/dscm 8.19E-04 1.25E-03 6.44E-04 0.001

mg/dscm@7%O2 7.80E-04 1.21E-03 6.17E-04 0.001

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 111.8 159.6 71.2 114.200

Elb/hr 6.18E+01 8.68E+01 3.91E+01 62.567

lb/mmBtuO2 2.39E-02 3.43E-02 1.53E-02 0.025

mg/dscm 2.73E+01 3.87E+01 1.74E+01 27.800

mg/dscm@7%O2 2.60E+01 3.74E+01 1.67E+01 26.700

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.00352 0.00356 0.00242 0.003

Elb/hr 1.95E-03 1.94E-03 1.33E-03 0.002

lb/mmBtuO2 7.52E-07 7.65E-07 5.20E-07 0.000

mg/dscm 8.61E-04 8.63E-04 5.90E-04 0.001

mg/dscm@7%O2 8.20E-04 8.33E-04 5.66E-04 0.001

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.01164 0.01833 0.00985 0.013

Friday, January 14, 2011 Page 7 of 20
Elb/hr 6.43E-03 9.97E-03 5.41E-03 0.007

lb/mmBtuO2 2.49E-06 3.94E-06 2.11E-06 0.000

mg/dscm 2.85E-03 4.44E-03 2.40E-03 0.003

mg/dscm@7%O2 2.71E-03 4.29E-03 2.30E-03 0.003

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.01363 0.00941 0.00588 0.010

Elb/hr 7.53E-03 5.12E-03 3.23E-03 0.005

lb/mmBtuO2 2.91E-06 2.02E-06 1.26E-06 0.000

mg/dscm 3.33E-03 2.28E-03 1.43E-03 0.002

mg/dscm@7%O2 3.17E-03 2.20E-03 1.37E-03 0.002

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.00313 0.00411 0.00217 0.003

Elb/hr 1.73E-03 2.23E-03 1.19E-03 0.002

lb/mmBtuO2 6.69E-07 8.83E-07 4.66E-07 0.000

mg/dscm 7.65E-04 9.96E-04 5.29E-04 0.001

mg/dscm@7%O2 7.28E-04 9.61E-04 5.07E-04 0.001

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 4

Mass_mg 63.2 78.2 49.6 63.667

lb/mmBtuO2 1.63E-02 2.02E-02 1.32E-02 0.017

Compound: Filterable PM2.5

Average

RunNumber 1 2 4

Mass_mg 21.9 22.7 0.0216 14.874

lb/mmBtuO2 5.65E-03 5.86E-03 5.73E-06 0.004

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 4

Mass_mg 273.6 139.5 77.8 163.633

lb/mmBtuO2 7.06E-02 3.60E-02 2.06E-02 0.042

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 4

Mass_mg 1 0.9 1.2 1.033

lb/mmBtuO2 2.58E-04 2.32E-04 3.18E-04 0.000

Compound: Total Particulate

Average

RunNumber 1 2 4

Mass_mg 340.5 218.7 128.6 229.267

lb/mmBtuO2 8.79E-02 5.65E-02 3.41E-02 0.060

Friday, January 14, 2011 Page 8 of 20
Process Run Data

Compound: Total PM2.5

Average

RunNumber 1 2 4

Mass_mg 299.2 163.2 100.6 187.667

lb/mmBtuO2 7.72E-02 4.22E-02 2.67E-02 0.049

Friday, January 14, 2011 Page 9 of 20
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 0 Tons 0

10 Bituminous Coal Burned 0 Tons 0

11 Bituminous Coal Burned 0 Tons 0

12 Bituminous Coal Burned 0 Tons 0

2 Bituminous Coal Burned 0 Tons 0

3 Bituminous Coal Burned 0 Tons 0

4 Bituminous Coal Burned 0 Tons 0

5 Bituminous Coal Burned 0 Tons 0

6 Bituminous Coal Burned 0 Tons 0

7 Bituminous Coal Burned 0 Tons 0

8 Bituminous Coal Burned 0 Tons 0

9 Bituminous Coal Burned 0 Tons 0

1 Average Heat Input 2241.8 MMBtu/hr 0

10 Average Heat Input 2220.4 MMBtu/hr 0

11 Average Heat Input 2220.4 MMBtu/hr 0

12 Average Heat Input 2220.4 MMBtu/hr 0

2 Average Heat Input 2263.1 MMBtu/hr 0

3 Average Heat Input 2241.8 MMBtu/hr 0

4 Average Heat Input 2305.8 MMBtu/hr 0

5 Average Heat Input 2305.8 MMBtu/hr 0

6 Average Heat Input 2263.1 MMBtu/hr 0

7 Average Heat Input 2263.1 MMBtu/hr 0

8 Average Heat Input 2220.4 MMBtu/hr 0

9 Average Heat Input 2220.4 MMBtu/hr 0

1 Steam Output 0 1000 lb steam/hr 0

10 Steam Output 0 1000 lb steam/hr 0

11 Steam Output 0 1000 lb steam/hr 0

12 Steam Output 0 1000 lb steam/hr 0

2 Steam Output 0 1000 lb steam/hr 0

3 Steam Output 0 1000 lb steam/hr 0

4 Steam Output 0 1000 lb steam/hr 0

5 Steam Output 0 1000 lb steam/hr 0

6 Steam Output 0 1000 lb steam/hr 0

Friday, January 14, 2011 Page 10 of 20
7 Steam Output 0 1000 lb steam/hr 0

8 Steam Output 0 1000 lb steam/hr 0

9 Steam Output 0 1000 lb steam/hr 0

1 Fuel Oil Firing Rate 0 0

10 Fuel Oil Firing Rate 0 0

11 Fuel Oil Firing Rate 0 0

12 Fuel Oil Firing Rate 0 0

2 Fuel Oil Firing Rate 0 0

3 Fuel Oil Firing Rate 0 0

4 Fuel Oil Firing Rate 0 0

5 Fuel Oil Firing Rate 0 0

6 Fuel Oil Firing Rate 0 0

7 Fuel Oil Firing Rate 0 0

8 Fuel Oil Firing Rate 0 0

9 Fuel Oil Firing Rate 0 0

1 Standard Pressure 0 atm 0

10 Standard Pressure 0 atm 0

11 Standard Pressure 0 atm 0

12 Standard Pressure 0 atm 0

2 Standard Pressure 0 atm 0

3 Standard Pressure 0 atm 0

4 Standard Pressure 0 atm 0

5 Standard Pressure 0 atm 0

6 Standard Pressure 0 atm 0

7 Standard Pressure 0 atm 0

8 Standard Pressure 0 atm 0

9 Standard Pressure 0 atm 0

1 Standard Temperature 177 Deg F 0

10 Standard Temperature 178 Deg F 0

11 Standard Temperature 178 Deg F 0

12 Standard Temperature 178 Deg F 0

2 Standard Temperature 177 Deg F 0

3 Standard Temperature 177 Deg F 0

4 Standard Temperature 177 Deg F 0

5 Standard Temperature 177 Deg F 0

6 Standard Temperature 177 Deg F 0

Friday, January 14, 2011 Page 11 of 20
APCD Run Data

Process Lab Run Data

7 Standard Temperature 0 Deg F 0

8 Standard Temperature 0 Deg F 0

9 Standard Temperature 178 Deg F 0

1 Unit Gross Electrical Output 255 MW 0

10 Unit Gross Electrical Output 255 MW 0

11 Unit Gross Electrical Output 255 MW 0

12 Unit Gross Electrical Output 255 MW 0

2 Unit Gross Electrical Output 255 MW 0

3 Unit Gross Electrical Output 255 MW 0

4 Unit Gross Electrical Output 255 MW 0

5 Unit Gross Electrical Output 255 MW 0

6 Unit Gross Electrical Output 255 MW 0

7 Unit Gross Electrical Output 255 MW 0

8 Unit Gross Electrical Output 254 MW 0

9 Unit Gross Electrical Output 254 MW 0

1 Unit Net Electric Generation 0 MWh 0

10 Unit Net Electric Generation 0 MWh 0

11 Unit Net Electric Generation 0 MWh 0

12 Unit Net Electric Generation 0 MWh 0

2 Unit Net Electric Generation 0 MWh 0

3 Unit Net Electric Generation 0 MWh 0

4 Unit Net Electric Generation 0 MWh 0

5 Unit Net Electric Generation 0 MWh 0

6 Unit Net Electric Generation 0 MWh 0

7 Unit Net Electric Generation 178 MWh 0

8 Unit Net Electric Generation 178 MWh 0

9 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 11014 Btu/lb

1 Fuel Moisture 12 %

1 Fuel Mercury Content 0 ppm

1 Fuel Cadmium Content 0 ppm

Friday, January 14, 2011 Page 12 of 20
1 Ultimate/Proximate Analysis

0

1 Fuel Nickel Content0 ppm

1 Fuel Arsenic Content0 ppm

1 Fuel Chromium Content0 ppm

1 Fuel Beryllium Content0 ppm

1 Fuel Lead Content0 ppm

1 Fuel Manganese Content0 ppm

1 Fuel Chlorine Content 42 ppm 1 Fuel Fluorine Content 32 ppm 5 Fuel Higher Heating Value 11083 Btu/lb 5 Fuel Moisture 13 % 5 Fuel Mercury Content 0.076 ppm 5 Fuel Cadmium Content 0.5 ppm 5 Ultimate/Proximate Analysis 0 5 Fuel Nickel Content 9.8 ppm 5 Fuel Arsenic Content 5.4 ppm 5 Fuel Chromium Content 5.3 ppm 5 Fuel Beryllium Content 0.65 ppm 5 Fuel Lead Content 2.8 ppm 5 Fuel Manganese Content 22 ppm 5 Fuel Chlorine Content 50 ppm 5 Fuel Fluorine Content 0 ppm 6 Fuel Higher Heating Value 11236 Btu/lb 6 Fuel Moisture 14.1 % 6 Fuel Mercury Content 0.052 ppm 6 Fuel Cadmium Content 0.5 ppm 6 Ultimate/Proximate Analysis 0 6 Fuel Nickel Content 6.9 ppm 6 Fuel Arsenic Content 20 ppm 6 Fuel Chromium Content 3.6 ppm 6 Fuel Beryllium Content 0.5 ppm 6 Fuel Lead Content 1.8 ppm 6 Fuel Manganese Content 29 ppm 6 Fuel Chlorine Content 50 ppm 6 Fuel Fluorine Content 0 ppm 7 Fuel Higher Heating Value 10388 Btu/lb 7 Fuel Moisture 9.6 % 7 Fuel Mercury Content 0 ppm 7 Fuel Cadmium Content 0 ppm 7 Ultimate/Proximate Analysis 0 7 Fuel Nickel Content 0 ppm 7 Fuel Arsenic Content 0 ppm 7 Fuel Chromium Content 0 ppm

Friday, January 14, 2011 Page 13 of 20
7 Fuel Beryllium Content

0 ppm

7 Fuel Lead Content0 ppm

7 Fuel Manganese Content0 ppm

7 Fuel Chlorine Content0 ppm

7 Fuel Fluorine Content0 ppm

8 Fuel Higher Heating Value 10452 Btu/lb 8 Fuel Moisture 10 % 8 Fuel Mercury Content 0 ppm 8 Fuel Cadmium Content 0 ppm 8 Ultimate/Proximate Analysis 0 8 Fuel Nickel Content 0 ppm 8 Fuel Arsenic Content 0 ppm 8 Fuel Chromium Content 0 ppm 8 Fuel Beryllium Content 0 ppm 8 Fuel Lead Content 0 ppm 8 Fuel Manganese Content 0 ppm 8 Fuel Chlorine Content 0 ppm 8 Fuel Fluorine Content 0 ppm 9 Fuel Higher Heating Value 10373 Btu/lb 9 Fuel Moisture 11 % 9 Fuel Mercury Content 0 ppm 9 Fuel Cadmium Content 0 ppm 9 Ultimate/Proximate Analysis 0 9 Fuel Nickel Content 0 ppm 9 Fuel Arsenic Content 0 ppm 9 Fuel Chromium Content 0 ppm 9 Fuel Beryllium Content 0 ppm 9 Fuel Lead Content 0 ppm 9 Fuel Manganese Content 0 ppm 9 Fuel Chlorine Content 0 ppm 9 Fuel Fluorine Content 0 ppm

10 Fuel Higher Heating Value 10699 Btu/lb

10 Fuel Moisture 12%

10 Fuel Mercury Content 0.105 ppm

10 Fuel Cadmium Content 0.59 ppm

10 Ultimate/Proximate Analysis0

10 Fuel Nickel Content 7.3 ppm

10 Fuel Arsenic Content 5.1 ppm

10 Fuel Chromium Content 4.4 ppm

10 Fuel Beryllium Content 0.59 ppm

10 Fuel Lead Content 2.6 ppm

10 Fuel Manganese Content 25 ppm

10 Fuel Chlorine Content 51 ppm

Friday, January 14, 2011 Page 14 of 20
10 Fuel Fluorine Content

0 ppm

11 Fuel Higher Heating Value 10601 Btu/lb

11 Fuel Moisture 12%

11 Fuel Mercury Content 0.05 ppm

11 Fuel Cadmium Content 0.74 ppm

11 Ultimate/Proximate Analysis0

11 Fuel Nickel Content 8.6 ppm

11 Fuel Arsenic Content 8.2 ppm

11 Fuel Chromium Content 4.7 ppm

11 Fuel Beryllium Content 0.62 ppm

11 Fuel Lead Content 2.5 ppm

11 Fuel Manganese Content 25 ppm

11 Fuel Chlorine Content 44 ppm

11 Fuel Fluorine Content0 ppm

12 Fuel Higher Heating Value 10460 Btu/lb

12 Fuel Moisture 12%

12 Fuel Mercury Content 0.067 ppm

12 Fuel Cadmium Content 0.54 ppm

12 Ultimate/Proximate Analysis0

12 Fuel Nickel Content 7.8 ppm

12 Fuel Arsenic Content 6.1 ppm

12 Fuel Chromium Content 4.4 ppm

12 Fuel Beryllium Content 0.59 ppm

12 Fuel Lead Content 2.2 ppm

12 Fuel Manganese Content0 ppm

12 Fuel Chlorine Content 49 ppm

12 Fuel Fluorine Content0 ppm

2 Fuel Higher Heating Value 10850 Btu/lb 2 Fuel Moisture 14 % 2 Fuel Mercury Content 0 ppm 2 Fuel Cadmium Content 0 ppm 2 Ultimate/Proximate Analysis 0 2 Fuel Nickel Content 0 ppm 2 Fuel Arsenic Content 0 ppm 2 Fuel Chromium Content 0 ppm 2 Fuel Beryllium Content 0 ppm 2 Fuel Lead Content 0 ppm 2 Fuel Manganese Content 0 ppm 2 Fuel Chlorine Content 42 ppm 2 Fuel Fluorine Content 33 ppm 3 Fuel Higher Heating Value 10736 Btu/lb 3 Fuel Moisture 13 % 3 Fuel Mercury Content 0 ppm

Friday, January 14, 2011 Page 15 of 20
3 Fuel Cadmium Content 0 ppm

3 Ultimate/Proximate Analysis 0

3 Fuel Nickel Content 0 ppm

3 Fuel Arsenic Content 0 ppm

3 Fuel Chromium Content 0 ppm

3 Fuel Beryllium Content 0 ppm

3 Fuel Lead Content 0 ppm

3 Fuel Manganese Content 0 ppm

3 Fuel Chlorine Content 49 ppm

3 Fuel Fluorine Content 41 ppm

4 Fuel Higher Heating Value 11150 Btu/lb

4 Fuel Moisture 12.8 %

4 Fuel Mercury Content 0.071 ppm

4 Fuel Cadmium Content 0.5 ppm

4 Ultimate/Proximate Analysis 0

4 Fuel Nickel Content 8.5 ppm

4 Fuel Arsenic Content 4.4 ppm

4 Fuel Chromium Content 4.8 ppm

4 Fuel Beryllium Content 0.5 ppm

4 Fuel Lead Content 2.1 ppm

4 Fuel Manganese Content 21 ppm

4 Fuel Chlorine Content 50 ppm

4 Fuel Fluorine Content 0 ppm

Friday, January 14, 2011 Page 16 of 20
Sampling / Stack Data Results Detail

Location Stack Exit - Method 25A

Average

Run Number 1 2 3

Test Date 3/12/2010 3/12/2010 3/12/2010

Run Start Time

Run Finish Time

Carbon Dioxide, % 12.5 12.3 12.7 12.500

Oxygen, % 6 6.8 6.1 6.300

Fuel Factor 0 1.15 1.17

Dry Volumetric Flow Rate, dry scfm 0 0 0 0.000

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13 13.1 12.8 12.967

Analyzer Make California California California

Analyzer Model 300-HFID 300-HFID 300-HFID

Analyzer Serial Number R01034 R01034 R01034

Operating Range 0 0 0 0.000

Operating Units

No. Readings/Avg. 0 0 0 0.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID CC169507 CC169507 CC169507

Calibration Pre Zero Cylinder Instrument Response -0.4 0.03 0.19 -0.060

Calibration Pre Zero Cylinder Bias -1.33 0.1 0.63 -0.200

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC115697 CC115697 CC115697

Calibration Pre High Cylinder Instrument Response 9.2 8.33 9.06 8.863

Calibration Pre High Cylinder Bias 0 -2.9 -0.47 -1.123

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC169507 CC169507 CC169507

Calibration Post Zero Cylinder Instrument Response 0 0.19 0.3 0.163

Calibration Post Zero Cylinder Bias 0 0.63 1 0.543

Calibration Post Zero Cylinder Drift 1.33 0.53 0.37 0.743

Calibration Post High Cylinder ID CC115697 CC115697 CC115697

Calibration Post High Cylinder Instrument Response 8.3 9.06 9 8.787

Calibration Post High Cylinder Bias -3 -0.47 -0.67 -1.380

Calibration Post High Cylinder Drift 3 2.43 0.2 1.877

Cavg 0.07 1.34 1.13 0.847

Cavg Units ppmvw ppmvw ppmvw

Cgas 0.3155 1.5003 1.0513 0.956

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0.2745251396

64805

1.303785672

68492

0.916733067

729083

0.832

Cgasw Units ppmvw ppmvw ppmvw

Friday, January 14, 2011 Page 17 of 20
Location Stack Exit - Method 26A

Average

Run Number 1 2 3

Test Date 3/3/2010 3/4/2010 3/4/2010

Run Start Time 1:30:00 PM 9:07:00 AM 1:45:00 PM

Run Finish Time 6:09:00 PM 12:41:00 PM 5:25:00 PM

Net Traversing Points 36 36 36

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.193 0.193 0.193 0.193

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 1.03 1.03 1.030

Barometric Pressure, inches of Mercury 29.8 29.71 29.71 29.740

Average Orifice Meter Differential, inches H2O 1.12 1.17 1.15 1.147

Dry Gas Meter Volume Sampled, cubic feet 103.688 103.783 103.694 103.722

Average Dry Gas Meter Temperature, °F 99.89 98.03 99.39 99.103

Dry Gas Meter Volume Sampled, dscf 100.589 100.725 100.389 100.568

Total Moisture Liquid collected, g 342.5 349.3 345.4 345.733

Volume of Water Vapor, standard cubic feet 16.12 16.44 16.26 16.273

Moisture Content of Stack Gas, % 13.81 14.03 13.94 13.927

Moisture Saturation at Stack Gas Temperature, % 49.22 50.08 49.64 49.647

Dry Mole Fraction 0.8619 0.8597 0.8606 0.861

Carbon Dioxide, % 12.4 13.4 11.4 12.400

Oxygen, % 6 5 7.4 6.133

Carbon Monoxide & Nitrogen, % 81.6 81.6 81.2 81.467

Fuel Factor 1.20 1.19 1.18

Dry Molecular Weight, lb/lb-Mole 30.22 30.34 30.12 30.227

Wet Molecular weight, lb/lb-Mole 28.53 28.61 28.43 28.523

Flue Gas Static Pressure, inches of H2O -0.91 -0.91 -0.91 -0.910

Absolute Flue Gas Pressure, inches of Mercury 29.73 29.64 29.64 29.670

Average Stack Gas Temperature, °F 178.11 178.75 178.36 178.407

Average Velocity Head, inches of H2O 1.1082786328

5216

1.153786574

27476

1.137325524

14198

1.133

Average Stack Gas Velocity, feet/second 65.57 66.95 66.66 66.393

Stack Cross-Sectional Area, square feet 201.062 201.062 201.062 201.062

Dry Volumetric Flow Rate, dry scfm 560,550.8 568,588.9 567,064.9 565,401.533

Actual Wet Volumetric Flue Gas Flow Rate, acfm 791,018.1 807,666.1 804,167.6 800,950.600

Percent Isokinetic of Sampling Rate, % 98.7 97.4 97.3 97.800

Percent Excess Air, % 38.6 30.2 52.7 40.500

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 192 192 192

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 14, 2011 Page 18 of 20
Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 7/29/2010 7/29/2010 7/30/2010

Run Start Time 8:25:00 AM 4:20:00 PM 11:00:00 AM

Run Finish Time 12:48:00 PM 10:32:00 PM 3:18:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.193 0.193 0.193 0.193

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.985 0.985 0.985 0.985

Barometric Pressure, inches of Mercury 30.01 30.01 29.96 29.993

Average Orifice Meter Differential, inches H2O 1.24 1.25 1.23 1.240

Dry Gas Meter Volume Sampled, cubic feet 153.115 154.169 153.065 153.450

Average Dry Gas Meter Temperature, °F 94.61 93.63 92.35 93.530

Dry Gas Meter Volume Sampled, dscf 144.452 145.707 144.751 144.970

Total Moisture Liquid collected, g 499 535 484.3 506.100

Volume of Water Vapor, standard cubic feet 23.49 25.18 22.80 23.823

Moisture Content of Stack Gas, % 13.99 14.73 13.61 14.110

Moisture Saturation at Stack Gas Temperature, % 55.61 55.48 56.94 56.010

Dry Mole Fraction 0.8601 0.8527 0.8639 0.859

Carbon Dioxide, % 11.7 12.1 12.2 12.000

Oxygen, % 6.3 6.5 6.4 6.400

Carbon Monoxide & Nitrogen, % 82 81.4 81.4 81.600

Fuel Factor 1.25 1.19 1.19

Dry Molecular Weight, lb/lb-Mole 30.12 30.20 30.21 30.177

Wet Molecular weight, lb/lb-Mole 28.42 28.40 28.55 28.457

Flue Gas Static Pressure, inches of H2O -0.85 -0.85 -0.85 -0.850

Absolute Flue Gas Pressure, inches of Mercury 29.95 29.95 29.90 29.933

Average Stack Gas Temperature, °F 183.96 183.85 184.96 184.257

Average Velocity Head, inches of H2O 1.2868289829

2835

1.288555652

04825

1.274438314

62518

1.283

Average Stack Gas Velocity, feet/second 70.86 70.92 70.47 70.750

Stack Cross-Sectional Area, square feet 201.062 201.062 201.062 201.062

Dry Volumetric Flow Rate, dry scfm 603,450.4 598,867.4 600,841.2 601,053.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 854,835.2 855,559.0 850,130.3 853,508.167

Percent Isokinetic of Sampling Rate, % 98.7 100.3 99.3 99.433

Percent Excess Air, % 41.0 43.4 42.4 42.267

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 192 192 192

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 14, 2011 Page 19 of 20
Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 4

Test Date 7/29/2010 7/29/2010 7/31/2010

Run Start Time 12:09:36 AM 3:15:00 PM 9:00:00 AM

Run Finish Time 1:58:54 PM 9:49:09 PM 3:28:09 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 366.67 370.35 363

Nozzle Diameter, inches 0.136 0.136 0.136 0.136

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.02 1.02 1.02 1.020

Barometric Pressure, inches of Mercury 30.01 30.01 29.9 29.973

Average Orifice Meter Differential, inches H2O 0.36 0.36 0.36 0.360

Dry Gas Meter Volume Sampled, cubic feet 121.823 123.537 119.543 121.634

Average Dry Gas Meter Temperature, °F 90.83 91.33 89.92 90.693

Dry Gas Meter Volume Sampled, dscf 119.573 121.145 117.099 119.272

Total Moisture Liquid collected, g 414 421.8 410.5 415.433

Volume of Water Vapor, standard cubic feet 19.49 19.85 19.32 19.553

Moisture Content of Stack Gas, % 14.02 14.08 14.16 14.087

Moisture Saturation at Stack Gas Temperature, % 57.41 56.27 52.39 55.357

Dry Mole Fraction 0.8598 0.8592 0.8584 0.859

Carbon Dioxide, % 11.7 12.1 12.5 12.100

Oxygen, % 6.3 6.5 6.4 6.400

Carbon Monoxide & Nitrogen, % 82 81.4 81.1 81.500

Fuel Factor 1.25 1.19 1.16

Dry Molecular Weight, lb/lb-Mole 30.12 30.20 30.26 30.193

Wet Molecular weight, lb/lb-Mole 28.42 28.48 28.52 28.473

Flue Gas Static Pressure, inches of H2O -0.88 -0.85 -0.88 -0.870

Absolute Flue Gas Pressure, inches of Mercury 29.95 29.95 29.84 29.913

Average Stack Gas Temperature, °F 185.42 184.50 181.08 183.667

Average Velocity Head, inches of H2O 1.3888109794

7548

1.379039461

24314

1.353848903

01649

1.374

Average Stack Gas Velocity, feet/second 73.69 73.30 72.52 73.170

Stack Cross-Sectional Area, square feet 201.062 201.062 201.062 201.062

Dry Volumetric Flow Rate, dry scfm 625,913.0 623,054.1 616,861.5 621,942.867

Actual Wet Volumetric Flue Gas Flow Rate, acfm 888,975.5 884,270.7 874,861.0 882,702.400

Percent Isokinetic of Sampling Rate, % 103.8 104.6 104.2 104.200

Percent Excess Air, % 41.0 43.4 42.6 42.333

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 192 192 192

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Friday, January 14, 2011 Page 20 of 20