EMISSIONS TEST REPORT 

POLK POWER STATION 

UNIT 1 

FACILITY ID NUMBER: 1050233 

EMISSION UNIT ID NO: -001 

SULFURIC ACID MIST (SAM) 

AUGUST 27 AND SEPTEMBER 1, 2009 

Prepared For: 

Tampa Electric Company 

Polk Power Station 

P.O. Box 111 

Tampa, Florida 33601-0111 

Prepared By: 

Tampa Electric Company 

Environmental, Health, & Safety 

Air Services Group 

Air Services Group 

5010 Causeway Boulevard 

Tampa, Florida 33619- 6130 
REPORT CERTIFICATION 

 The sampling and subsequent data entry/reduction detailed in this report 

was conducted at my direction, and I hereby certify that this test report is 

authentic and accurate to the best of my knowledge. 

Signature:__________________________ 

Scott E. Given 

Environmental Technician 

Test Team Lead 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the test performance, associated quality assurance 

activities, the resultant calculations, and the contents of this report, and certify 

that all project quality objectives have been met. This report is approved for 

submittal. 

Signature:__________________________ 

Raymond A. McDarby, Jr. 

Senior Environmental Technician 

Quality Assurance/Quality Control Specialist 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the testing details and results submitted in this report, 

and hereby certify that this test report is authentic and accurate to the best of 

my knowledge. 

Signature:__________________________ 

David A. Smith, QSTI 

Coordinator – Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 
TABLE OF CONTENTS

SECTION PAGE NO.

1.0 INTRODUCTION 1 

2.0 DISCUSSION OF RESULTS 2 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES 3 

4.0 TABULATED RESULTS 

SULFURIC ACID MIST TEST SUMMARY 5 

NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 6 

HEAT INPUT CALCULATIONS 7 

5.0 STACK SAMPLING LOCATION DIAGRAM 9 

APPENDICES

A. SULFURIC ACID MIST TEST INFORMATION

CALCULATED RUN DATA 

LABORATORY ANALYSIS 

FIELD DATA SHEETS 

EQUIPMENT CALIBRATIONS 

B. TURBINE DATA (PLANT INFORMATION SYSTEM)

C. FUEL ANALYSIS

D. CEMS DATA

E. TEST PARTICIPANTS
1 

1.0 INTRODUCTION

On August 27, 2009 and September 1, 2009, Tampa Electric Company’s, 

Environmental Services, Air Services Group performed Sulfuric Acid Mist (SAM) source 

emission tests on Unit No. 1 at the Polk Power Station. Unit No. 1 is an integrated coal 

gasification combined cycle (IGCC) generating unit. The combustion turbine was fired 

with syngas from the coal gasification system. A blend of petroleum coke and 

bituminous coal was gasified for this test. Testing was conducted according to United 

States Environmental Protection Agency (USEPA) test methods stipulated in 40 CFR 

Part 60, Appendix A and Florida Department of Environmental Protection (FDEP) 

Permit No. 1050233-016-AV. 

Nitrogen Oxides (NOx) and Sulfur Dioxide (SO2) data was taken from the Continuous 

Emissions Monitoring System’s (CEMS) Data Acquisition and Handling System (DAHS) 

and is presented as averages over the test period. 
2 

2.0 DISCUSSION OF RESULTS

The Sulfuric Acid Mist (H2SO4) emission rate was derived from five 1-hour test runs. 

The calculated average H2SO4 emission rate was 39 lbs/hr. The FDEP permitted 

emission rate is 55 lbs/hr based on a 30-day rolling average. 

Sulfur Dioxide (SO2) emissions during the sulfuric acid mist testing were determined to 

be 322 lbs/hr. 

Nitrogen Oxides (NOx) emissions during the sulfuric acid mist testing were determined 

to be 103 lbs/hr. 

During the tests on August 27, 2009, Unit No. 1 Combustion Turbine was operated at 

an average load of 170 megawatts and an average heat input of 1697 mmBtu/hr. 

During the tests on September 1, 2009, Unit No. 1 Combustion Turbine was operated at 

an average load of 170 megawatts and an average heat input of 1684 mmBtu/hr. The 

FDEP permitted heat input is 1755 mmBtu/hr, at an ambient temperature of 59o 

(corrected to 1750 mmBtu/hr based on an average inlet vane temperature of 80oF, and 

the manufacturer’s heat input correction curve for this unit). The calculated capacity 

factor during the test was 97% on August 27, 2009 and 96% on September 1, 2009. 
3 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generating Station is located at County Road 630 approximately 

13 miles southwest of Bartow, Polk County, Florida. Unit No. 1 is an IGCC generating 

unit, with a net capacity of 192 MW when fired with Syngas fuel. The source sampling 

location consists of a circular stack 19 feet in diameter with four sample ports located 90 

degrees apart on the stack circumference. A diagram of the stack sampling location is 

included along with other pertinent information on the test site. 

Sulfuric acid mist sampling and analysis was performed in accordance with USEPA 

Reference Method 8 (40 CFR Part 60, Appendix A) "Determination of Sulfuric Acid Mist 

and Sulfur Dioxide Emissions from Stationary Sources”, and FDEP Permit No. 1050233-

016-AV, Condition A.56. A total of eight runs were conducted during this test program. 

Runs 4, 5 and 6 were disqualified due to sample contamination. These three runs were 

excluded because the first impinger (IPA(80%), SO3/H2SO4 capture), gained volume. 

Water vapor, present in the flue gas, condensed in the first impinger. SO2 entering the 

first impinger was oxidized to SO3 by the water and trace amounts of H2O2 in the 

aqueous IPA solution. Flow data from the installed Continuous Emissions Monitor 

(CEM) was used to calculate the mass emissions. The flow CEM has been certified via 

Reference Method 2F using a 3-D flow probe to eliminate impacts of axial and nonradial flow from the measurement. The flow data was corrected to dry basis using the 

moisture number determined during the Reference Method 8 test. 

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. 

This data was taken as 1-minute averages over the time frame representing the time 

frame of the sulfuric acid mist test. 

Plant operational data was taken from the Plant Information (PI) server system. This 

data was taken as 1-minute averages representing the time frame of the sulfuric acid 

mist test. Data captured included the average unit load, average fuel flow, average inlet 

vane temperature, and average saturator readings. Details are included in Appendix B. 
4 

4.0 TABULATED RESULTS
Air Services 

Customer: Polk Power StationFacility: Unit 1Sampling Location: StackOperating Conditions: Full LoadTest Date:

Run #1 Run #2 Run #3 Run #4 Run #5 Run #6 Run #7 Run #8 A

Sampled Volume, Vm(std), dscf: 37.31 37.24 37.71 37.67 36.90 27.44 38.26 38.42 

Stack Moisture, Bws x 100, %: 5.5 6.8 6.6 12.0 11.0 7.3 9.2 8.0 

Isokinetic Sampling Rate, I, %: 100.8 101.7 101.8 106.8 105.3 101.5 103.4 102.3 

C H2SO4, lb/dscf: 5.9E-07 9.3E-07 1.3E-06 1.3E-06 1.4E-06 1.3E-06 9.6E-07 7.7E-07 

Stack Flow (Flow CEM), dscfm: 725000 719000 721000 680000 691000 717000 704000 705000

E H2SO4, lbs/hr (w/ Flow CEM): 26 40 58 53 59 55 40 33 

Adjusted Average (Runs 4, 5, and 6 excluded): 

E H2SO4, is calculated as CH2SO4, lbs/dscf times Stack Flow (Flow CEM), dscfm times 60 minutes/hour.

Stack Flow (Flow CEM), dscfm is Stack Flow from DAHS corrected to the Reference Method 8 measured moisture.

Sulfuric Acid Mist - Reference Method 8

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Summary

August 27, 2009 September 1, 2009

5 
POLK POWER STATION

NO X & SO 2 COMPLIANCE DATA FROM CEMS

NOx SO2 Flow NOx SO2

ppmvw ppmvw kscfmw lbs/hr lbs/hr

20.1 43.5 771 111 334

NOx SO2 Flow NOx SO2

ppmvw ppmvw kscfmw lbs/hr lbs/hr

17.3 40.3 771 95.6 309

Test Average: 103 322

NOX, lbs/hr calculated as:

NOX, ppmvw x 1.194E-07 x Flow, kscfmw x 60 min/hr x 1000/k

SO2, lbs/hr calculated as:

SO2, ppmvw x 1.660E-07 x Flow, kscfmw x 60 min/hr x 1000/k

September 1, 2009

CEM Data Calculated Data

HEAT RECOVERY STEAM GENERATOR

UNIT 1

August 27, 2009

CEM Data Calculated Data

6 
POLK POWER STATION

HEAT INPUT CALCULATION

Average fuel flow: 6529 Kcfh

Mole weight correction to meter cal: 0.9883 mole weight correction factor

Corrected fuel flow:1 6453 Kcfh, corrected for density

Average moisture: 0.28 % H20 added to fuel

Corrected fuel flow:2 6435 Kscfh, corrected for moisture

Gross heating value of fuel (HHV): 263.7 Btu/scf

Heat Input: 1697 mmBtu/hr

Average fuel flow: 6587 Kcfh

Mole weight correction to meter cal: 0.9883 mole weight correction factor

Corrected fuel flow:1 6510 Kcfh, corrected for density

Average moisture: 1.93 % H20 added to fuel

Corrected fuel flow:2 6385 Kscfh, corrected for moisture

Gross heating value of fuel (HHV): 263.7 Btu/scf

Heat Input: 1684 mmBtu/hr

 Mole weight correction factor to meter calibration is taken from ratio of syngas

mole weight to calibration gas mole weight.

September 1, 2009

Average fuel flow from Plant Information Data Base.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

August 27, 2009

1Average fuel flow times mole weight correction factor.

2Corrected fuel flow times (1 - (Average moisture / 100)).

Gross Heating value of fuel (HHV) is from fuel analysis.

Heat input is (HHV x Corrected fuel flow) / 1000.

7 
8 

5.0 SAMPLING LOCATION TRAVERSE DIAGRAM
9 

UNFIRED HEAT

RECOVERY

BOILER

TRANSITION

DUCT

EXHAUST FROM

TURBINE

14 FT.

38 FT.

150 FT.

136 FT.

 PORT LOCATION PLAN

19.0 FT.ID.

STACK DIAMETERS DOWNSTREAM

FROM DISTURBANCE = 2.0

STACK DIAMETERS UPSTREAM

FROM DISTURBANCE = 0.7

STACK DIAMETER = 19.0 FT.

STACK AREA = 283.529 SQ. FT.

STACK AREA =40828.138 SQ. IN.

 TRAVERSE 

 POINTS

 1 - 4.79 ”

 2 - 15.28 ”

 3 - 26.90 ”

 4 - 40.36 ”

 5 - 57.00 ”

 6 - 80.17 ”

 

 ADD 13” PORT LENGTH

 TO POINTS

Polk Power Station

Unit No. 1

IGCC

Test Location
APPENDIX A 

SULFURIC ACID MIST TEST INFORMATION 
CALCULATED RUN DATA 
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 1

Date: 08/27/2009

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.196 inches

Barometric Pressure, Pb: 29.80 "Hg Nozzle Area, An: 0.00020951 ft2

Stack Pressure, Ps: 29.74 "Hg Average Orifice Meter, ΔH: 1.288 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 37.623 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 70.9 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 327.8 o

F

10.5 % O2 Average √Δp: 1.139 "H2O

0.0 % CO Condensate Volume, Vlc: 45.7 ml

80.5 % N2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.154 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 37.310 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.055 %

FDA = 1.0 - Bws 0.945 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.86 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.21 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 100.8 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0102

Volume Titrant Blank, Vtb 0.85

Volume Titrant Sample, Vt 4.85

Volume of Sample Aliquot, Va 50

Total Volume of Solution, Vsoln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt - Vtb) x (Vsoln / Va)) / Vm(std) = 5.911E-07 lb/dscf

Stack Flow (Flow CEM), dscfm: 725000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 26 lb/hr
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 2

Date: 08/27/2009

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.196 inches

Barometric Pressure, Pb: 29.81 "Hg Nozzle Area, An: 0.00020951 ft2

Stack Pressure, Ps: 29.75 "Hg Average Orifice Meter, ΔH: 1.291 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 37.591 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 71.7 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 327.5 o

F

10.5 % O2 Average √Δp: 1.139 "H2O

0.0 % CO Condensate Volume, Vlc: 57.2 ml

80.5 % N2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.696 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 37.235 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.068 %

FDA = 1.0 - Bws 0.932 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.86 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.06 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 101.7 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0102

Volume Titrant Blank, Vtb 0.85

Volume Titrant Sample, Vt 7.1

Volume of Sample Aliquot, Va 50

Total Volume of Solution, Vsoln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt - Vtb) x (Vsoln / Va)) / Vm(std) = 9.254E-07 lb/dscf

Stack Flow (Flow CEM), dscfm: 719000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 40 lb/hr
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 3

Date: 08/27/2009

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.196 inches

Barometric Pressure, Pb: 29.81 "Hg Nozzle Area, An: 0.00020951 ft2

Stack Pressure, Ps: 29.75 "Hg Average Orifice Meter, ΔH: 1.318 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 38.095 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 72.1 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 328.8 o

F

10.5 % O2 Average √Δp: 1.152 "H2O

0.0 % CO Condensate Volume, Vlc: 56.4 ml

80.5 % N2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.659 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 37.710 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.066 %

FDA = 1.0 - Bws 0.934 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.86 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.08 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 101.8 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0102

Volume Titrant Blank, Vtb 0.85

Volume Titrant Sample, Vt 10

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt - Vtb) x (Vsoln / Va)) / Vm(std) = 1.338E-06 lb/dscf

Stack Flow (Flow CEM), dscfm: 721000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 58 lb/hr
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 4

Date: 08/27/2009

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.196 inches

Barometric Pressure, Pb: 29.81 "Hg Nozzle Area, An: 0.00020951 ft2

Stack Pressure, Ps: 29.75 "Hg Average Orifice Meter, ΔH: 1.314 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 37.986 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 71.2 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 330.3 o

F

10.5 % O2 Average √Δp: 1.152 "H2O

0.0 % CO Condensate Volume, Vlc: 108.8 ml

80.5 % N2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 5.129 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 37.667 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.120 %

FDA = 1.0 - Bws 0.880 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.86 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.44 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs 106.8 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0102

Volume Titrant Blank, Vtb 0.95

Volume Titrant Sample, Vt 9.8

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 1.295E-06 lb/dscf

Stack Flow (Flow CEM), dscfm: 680000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 53 lb/hr
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 5

Date: 08/27/2009

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.196 inches

Barometric Pressure, Pb: 29.80 "Hg Nozzle Area, An: 0.00020951 ft2

Stack Pressure, Ps: 29.77 "Hg Average Orifice Meter, ΔH: 1.264 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 37.270 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 71.8 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 331.0 o

F

10.5 % O2 Average √Δp: 1.131 "H2O

0.0 % CO Condensate Volume, Vlc: 92.8 ml

80.5 % N2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 4.375 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.900 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.106 %

FDA = 1.0 - Bws 0.894 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.86 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.60 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs 105.3 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0102

Volume Titrant Blank, Vtb 0.95

Volume Titrant Sample, Vt 10.4

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 1.412E-06 lb/dscf

Stack Flow (Flow CEM), dscfm: 691000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 59 lb/hr
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 6

Date: 08/27/2009

Sample Time, θ: 45 minutes Nozzle Diameter, Dn: 0.196 inches

Barometric Pressure, Pb: 29.75 "Hg Nozzle Area, An: 0.00020951 ft2

Stack Pressure, Ps: 29.69 "Hg Average Orifice Meter, ΔH: 1.263 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 27.730 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 71.2 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 330.6 o

F

10.5 % O2 Average √Δp: 1.130 "H2O

0.0 % CO Condensate Volume, Vlc: 46.0 ml

80.5 % N2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.168 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 27.436 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.073 %

FDA = 1.0 - Bws 0.927 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.86 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.99 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs 101.5 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0102

Volume Titrant Blank, Vtb 0.95

Volume Titrant Sample, Vt 7.35

Volume of Sample Aliquot, Va 50

Total Volume of Solution, Vsoln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 1.286E-06 lb/dscf

Stack Flow (Flow CEM), dscfm: 717000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 55 lb/hr
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 7

Date: 09/01/2009

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.198 inches

Barometric Pressure, Pb: 29.80 "Hg Nozzle Area, An: 0.00021381 ft2

Stack Pressure, Ps: 29.74 "Hg Average Orifice Meter, ΔH: 1.397 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 38.080 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 71.0 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 325.1 o

F

10.5 % O2 Average √Δp: 1.151 "H2O

0.0 % CO Condensate Volume, Vlc: 82.2 ml

80.5 % N2 Meter Box Y: 1.011 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 3.875 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 38.259 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.092 %

FDA = 1.0 - Bws 0.908 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.86 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.77 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs 103.4 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0099

Volume Titrant Blank, Vtb 0.01

Volume Titrant Sample, Vt 6.85

Volume of Sample Aliquot, Va 50

Total Volume of Solution, Vsoln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 9.566E-07 lb/dscf

Stack Flow (Flow CEM), dscfm: 704000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 40 lb/hr
Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 8

Date: 09/01/2009

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.198 inches

Barometric Pressure, Pb: 29.81 "Hg Nozzle Area, An: 0.00021381 ft2

Stack Pressure, Ps: 29.75 "Hg Average Orifice Meter, ΔH: 1.410 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 38.220 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 71.0 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 325.0 o

F

10.3 % O2 Average √Δp: 1.156 "H2O

0.0 % CO Condensate Volume, Vlc: 71.0 ml

80.7 % N2 Meter Box Y: 1.011 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 3.347 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 38.417 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.080 %

FDA = 1.0 - Bws 0.920 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.85 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.90 lb./lb. mole

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs 102.3 %

Data from Laboratory Analysis: H2SO4/SO3

Normality of Barium Chloride titrant, N 0.0099

Volume Titrant Blank, Vtb 0.01

Volume Titrant Sample, Vt 5.55

Volume of Sample Aliquot, Va 50

Total Volume of Solution, Vsoln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 7.716E-07 lb/dscf

Stack Flow (Flow CEM), dscfm: 705000 dscfm

E H2SO4 = C H2SO4 x Stack Flow x 60 = 33 lb/hr
LABORATORY ANALYSIS 
Laboratory Services

5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272

Report For:

Laboratory ID: AB02584

Date and Time Collected:

Sampled By:

Sample Information

Description:

Location Code:

Report Date: 10/6/2009

Polk Unit 1 SO2 Engineering Test

TE_PK_1_SO2ENGINEERING

Project Account Code:

Sample Collection Method: Date of Sample Receipt: 8/28/2009

Laboratory Results

8/27/2009 12:00:00 AM

PARAMETER Result

Qualifier

Code

Test

Method Analyst Units

Upper

MDL Limit

Violation

Check

Analysis

Date & Time

Lower

Limit

Normality of BaCl2 * 2H2O 0.0103 0.0001 KARXL 8/31/2009 2:30:00 PM

SO2, Avg. of Blank Titrations 0.01 milliliters 0.1 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Final Sample Volume see comment milliliters 0.1 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Run 1, Avg. of Titrations 15.25 milliliters 0.01 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Run 2, Avg. of Titrations 14.55 milliliters 0.01 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Run 3, Avg. of Titrations 16.10 milliliters 0.01 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Run 4, Avg. of Titrations 15.40 milliliters 0.01 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Run 5, Avg. of Titrations 13.80 milliliters 0.01 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Run 6, Avg. of Titrations 10.00 milliliters 0.01 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

SO2, Volume of Sample Aliquot see comment milliliters 0.1 EPA Method 6 KARXL 8/31/2009 2:30:00 PM

Comments

Designee for Peggy Penner,

Manager, Laboratory Services

All results calculated on a wet to wet basis, unless otherwise indicated.

Runs 1, 2, 3, 4, 5 and the field blank have final

sample volumes of 500ml.

Run 6 has a final sample volume of 250ml.

Runs 1, 2, 3, 4, 5 and the field blank all have sample aliquots of 20ml.

Run 6 has a sample aliquot of 10ml.

Should there be any questions regarding this report, please contact:

(813) 630-7490

Cheryl Howard,

Report Number: Page 1 of 1 "General Report" AB02584-100609-09

Laboratory Services certifies that the test results in this report meet all requirements of the NELAC standards, unless indicated otherwise

in the body of the report. Unless otherwise noted, all methods followed are per the most current published version of 40 CFR Part 136, Table B.

Results reported on this report pertain to the above referenced sample only.
Laboratory Services

5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272

Report For:

Laboratory ID: AB02640

Date and Time Collected:

Sampled By:

Sample Information

Description: JORGE VARINO

Location Code:

Report Date: 10/6/2009

Polk Unit 1 SO3 Engineering Test

TE_PK_1_SO3ENGINEERING

Project Account Code:

Sample Collection Method: Date of Sample Receipt: 9/2/2009

Laboratory Results

9/1/2009 12:00:00 PM

PARAMETER Result

Qualifier

Code

Test

Method Analyst Units

Upper

MDL Limit

Violation

Check

Analysis

Date & Time

Lower

Limit

Normality of BaCl2 * 2H2O 0.0099 0.0001 KARXL 9/2/2009 10:30:00 AM

SO3, Avg. of Blank Titrations 0.01 milliliters 0.01 I EPA - Meth.8 KARXL 9/2/2009 10:30:00 AM

SO3, Run #1, Avg. of Titrations 6.85 milliliters 0.01 EPA - Meth.8 KARXL 9/2/2009 10:30:00 AM

SO3, Run #2, Avg. of Titrations 5.55 milliliters 0.01 EPA - Meth.8 KARXL 9/2/2009 10:30:00 AM

SO3, Volume of Contained Sample 250 milliliters 1 EPA - Meth.8 KARXL 9/2/2009 10:30:00 AM

SO3, Volume of Sample Aliquot 50 milliliters 0.1 EPA - Meth.8 KARXL 9/2/2009 10:30:00 AM

Comments

Designee for Peggy Penner,

Manager, Laboratory Services

I - The reported value is between the laboratory method detection limit (MDL) and the laboratory practical quantitation limit (PQL). PQL = 4 x MDL.

All results calculated on a wet to wet basis, unless otherwise indicated.

Data Qualifier Codes Explanation:

Should there be any questions regarding this report, please contact:

(813) 630-7490

Cheryl Howard,

Report Number: Page 1 of 1 "General Report" AB02640-100609-09

Laboratory Services certifies that the test results in this report meet all requirements of the NELAC standards, unless indicated otherwise

in the body of the report. Unless otherwise noted, all methods followed are per the most current published version of 40 CFR Part 136, Table B.

Results reported on this report pertain to the above referenced sample only.
FIELD DATA SHEETS 








EQUIPMENT CALIBRATIONS 
Air Services Group

SUMMARY OF EQUIPMENT CALIBRATIONS

EQUIPMENT CAL DATE METHOD RESULTS

CONSOLE (MB 06) USEPA RM 5

INITIAL 08/04/2009 (ORIFICE) 0.998

POST TEST 08/31/2009 0.998

CONSOLE (MB 08) USEPA RM 5

INITIAL 08/04/2009 (ORIFICE) 1.011

POST TEST 09/18/2009 1.010

NOZZLE (SN06) CALIPER 

INITIAL 08/03/2009 MEASUREMENTS 0.196

POST TEST 08/28/2009 0.195

NOZZLE (SN16) CALIPER 

INITIAL 08/03/2009 MEASUREMENTS 0.198

POST TEST 09/03/2009 0.198

PYROMETER (PY 10) 08/04/2009 ASTM THERMOMETER + 2o

 F

PYROMETER (PY 20) 08/04/2009 ASTM THERMOMETER + 2o

 F

PITOT TUBE (PT 11) 08/04/2009 USEPA RM 2 Cp = 0.84

PITOT TUBE (PT 12) 08/04/2009 USEPA RM 2 Cp = 0.84

BAROMETER (BR 06) 08/07/2009 NWS COMPARISON + 0.01" Hg
Environmental Services

Air Services Group

Red Team

Manufacturer: Thermo Anderson Calibration Date:

Model Number:MST-C1 Barometric Pressure: 30.07 "Hg

Instrument Code Number: ^MB06 Theoretical Critical Vacuum: 14.18 "Hg

LabWorks Sample Number: Calibrated By:

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

1.95 15 372.800 384.439 11.639 66 71 64 71

1.20 15 384.439 393.437 8.998 70 72 70 74

0.62 15 393.437 400.173 6.736 74 75 74 77

3.60 15 400.173 416.022 15.849 69 77 60 76

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

63 0.5923 19.5 70 70 70.0

55 0.4596 21.0 70 70 70.0

48 0.3452 23.0 70 70 70.0

73 0.8106 16.0 70 70 70.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

11.748 11.605 11.595 0.988 -0.010 1.842 0.037

9.006 9.005 8.997 1.000 0.002 1.870 0.065

6.689 6.763 6.758 1.011 0.013 1.701 -0.104

15.987 15.882 15.869 0.993 -0.005 1.807 0.002

Averages: 0.998 1.805

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

Quarterly Calibration

08/04/2009

SEG

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.

IMPORTANT

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice Readings

Ambient Temperatures

CALCULATED DATA

Critical Orifice
Environmental Services

Air Services Group

Manufacturer: Thermo Calibration Date:

Model Number:MST Barometric Pressure: 29.99 "Hg

Instrument Code Number: MB06 Theoretical Critical Vacuum: 14.15 "Hg

LabWorks Sample Number: Calibrated By:

Associated Test: Team: RED

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

1.2 10 778.000 784.000 6.000 69 74 69 74

1.2 10 784.000 790.010 6.010 69 74 69 75

1.2 10 790.010 796.025 6.015 69 75 69 75

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

55 0.4596 21.0 71 71 71.0

55 0.4596 21.0 71 71 71.0

55 0.4596 21.0 71 71 71.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

5.990 5.981 6.004 0.999 0.001 1.879 0.001

5.997 5.981 6.004 0.997 0.000 1.878 0.000

5.999 5.981 6.004 0.997 -0.001 1.877 -0.001

Averages: 0.998 1.878

Prior Y: 0.998

% Difference:(+/-5%) 0.03% PASS

CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

RJN

08/31/2009

POST - TEST CALIBRATION CHECK

Ambient Temperatures

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

Critical Orifice Readings

IMPORTANT

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.
Environmental Services

Air Services Group

Blue Team

Manufacturer: APEX Calibration Date:

Model Number: 522 Barometric Pressure: 30.07 "Hg

Instrument Code Number: ^MB08 Theoretical Critical Vacuum: 14.18 "Hg

LabWorks Sample Number: Calibrated By:

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

0.70 15 786.800 793.426 6.626 68 68 68 68

3.60 15 793.426 809.011 15.585 69 69 72 72

2.00 15 809.011 820.463 11.452 71 71 72 72

1.20 15 820.463 829.370 8.907 72 72 72 72

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

48 0.3452 22.0 70 70 70.0

73 0.8106 17.0 70 70 70.0

63 0.5923 19.0 70 70 70.0

55 0.4596 21.0 70 70 70.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

6.668 6.763 6.758 1.014 0.003 1.946 0.072

15.720 15.882 15.869 1.010 -0.001 1.807 -0.068

11.485 11.605 11.595 1.010 -0.001 1.877 0.002

8.907 9.005 8.997 1.011 -0.001 1.868 -0.006

Averages: 1.011 1.875

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

Quarterly Calibration

08/04/2009

SEG

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.

IMPORTANT

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice Readings

Ambient Temperatures

CALCULATED DATA

Critical Orifice
Environmental Services

Air Services Group

Manufacturer: Apex Calibration Date:

Model Number: 522 Barometric Pressure: 29.98 "Hg

Instrument Code Number: mb08 Theoretical Critical Vacuum: 14.14 "Hg

LabWorks Sample Number: Calibrated By:

Associated Test: Team: RED

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

1.2 10 437.300 443.215 5.915 69 69 69 69

1.2 10 443.215 449.125 5.910 69 69 70 70

1.2 10 449.125 455.040 5.915 70 70 71 71

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

55 0.4596 21.0 71 71 71.0

55 0.4596 21.0 71 71 71.0

55 0.4596 21.0 71 71 71.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

5.931 5.979 6.004 1.008 -0.002 1.888 0.002

5.920 5.979 6.004 1.010 0.000 1.886 0.001

5.914 5.979 6.004 1.011 0.001 1.883 -0.003

Averages: 1.010 1.886

Prior Y: 1.011

% Difference:(+/-5%) 0.12% PASS

BB-st4-ecotherm-(09-17-09)

IMPORTANT

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.

Ambient Temperatures

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

Critical Orifice Readings

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

SEG

09/18/2009

POST - TEST CALIBRATION CHECK

CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice
Environmental Services

Air Services Group

Shared Resource

Calibration Date: Responsible Party:

Nozzle Maximum Average

I.D. D1 D2 D3 Difference, " Dn, inches

^SN01 0.114 0.117 0.114 0.003 0.115

^SN04 0.127 0.127 0.127 0.000 0.127

^SN05 0.150 0.150 0.149 0.001 0.150

^SN06 0.195 0.197 0.196 0.002 0.196

^SN10 0.299 0.300 0.299 0.001 0.299

^SN12 0.388 0.386 0.387 0.002 0.387

^SN15 0.164 0.164 0.164 0.000 0.164

^SN16 0.197 0.198 0.198 0.001 0.198

^SN19 0.280 0.281 0.279 0.002 0.280

^SN22 0.369 0.369 0.369 0.000 0.369

^SN30 0.314 0.313 0.314 0.001 0.314

^SN36 0.187 0.187 0.188 0.001 0.187

^SN37 0.206 0.207 0.206 0.001 0.206

^SN38 0.249 0.251 0.249 0.002 0.250

^SN46 0.190 0.190 0.189 0.001 0.190

^SN47 0.202 0.201 0.202 0.001 0.202

^SN48 0.251 0.251 0.250 0.001 0.251

^SN50 0.311 0.313 0.313 0.002 0.312

^SN58 0.240 0.242 0.242 0.002 0.241

^SN68 0.246 0.247 0.247 0.001 0.247

^SN69 0.376 0.376 0.376 0.000 0.376

^SN70 0.616 0.616 0.615 0.001 0.616

^SN71 0.613 0.614 0.613 0.001 0.613

^SN72 0.377 0.377 0.377 0.000 0.377

^SN73 0.502 0.501 0.502 0.001 0.502

^SN74 0.485 0.485 0.482 0.003 0.484

^SN75 0.211 0.210 0.211 0.001 0.211

^SN76 0.249 0.249 0.248 0.001 0.249

^SN77 0.273 0.272 0.272 0.001 0.272

Nozzle Diameter, Dn (in)

QUARTERLY NOZZLE CALIBRATIONS

STEEL NOZZLE SET

08/03/2009 SEG
Environmental Services

Air Services Group

Shared Resource

Calibration Date:

Calibration Personnel:

Test Designation:

Maximum Average

D1 D2 D3 Difference, " Dn, inches

0.195 0.195 0.196 0.001 0.195

Data Notations: 

Maximum Difference must be < 0.004".

Quarterly (pre-test) value for nozzle ID SN06 was 0.196

Difference (Pre-test/Post-test) is: 0.001 PASS

SN06

POST TEST NOZZLE CALIBRATION 

Nozzle

Identifier

Nozzle Diameter, Dn (in)

08/28/2009

SEG

Polk 1 RM8 (08/27/09)
Environmental Services

Air Services Group

Shared Resource

Calibration Date:

Calibration Personnel:

Test Designation:

Maximum Average

D1 D2 D3 Difference, " Dn, inches

0.197 0.198 0.198 0.001 0.198

Quarterly (pre-test) value for nozzle ID SN 16 was 0.198

Difference (Pre-test/Post-test) is: 0.000

SN 16

POST TEST NOZZLE CALIBRATION 

Nozzle

Identifier

Nozzle Diameter, Dn (in)

03-Sep-09

McDarby

Polk SAM (1-Sep-2009)
Environmental Services

Air Services Group

Red Team

Pyrometer Under Test

Pyrometer Number: ^PY10

Labworks Sample #

Calibration Date: 08/04/2009

Calibrator Information

Calibrator Type/Manufacturer: Hart Scientific

Calibrator Serial Number: AOA024

Date of Last Calibration: 04/29/2009

Calibration Personnel (Typed and Signature):

Calibration Data

Calibration Reference Pyrometer

Point Temperature Indication Difference

1 400 401 -1

2 212 210 2

3 32 31 1

Reference temperatures must encompass the expected range of measurement. These three points

should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit.

Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration

Point Difference

1 Pass

2 Pass

3 Pass

0

SEG

Pyrometer Calibration
Air Services Group

Shared

Pyrometer Under Test

Pyrometer Number: ^PY20

Labworks Sample #

Calibration Date: 08/04/2009

Calibrator Information

Calibrator Type/Manufacturer: Hart Scientific

Calibrator Serial Number: AOA024

Date of Last Calibration: 04/29/2009

Calibration Personnel (Typed and Signature):

Calibration Data

Calibration Reference Pyrometer

Point Temperature Indication Difference

1 400 400 0

2 212 212 0

3 32 30 2

Reference temperatures must encompass the expected range of measurement. These three points

should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit.

Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration

Point Difference

1 Pass

2 Pass

3 Pass

N/A

SEG

Pyrometer Calibration
Pitot Tube ID #

Calibration Date Operating Quarter/Year: 3/09

Openings Damaged? ___ Y ___N Repaired? ____Y ___ N ___ N/A

Labworks #:

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 0.5 degrees Dt 0.48 < Dt > 0.95 cm

α 2 0.2 degrees α < 10 degrees

β 1 0.5 degrees

β 2 1 degrees

β1 < 5 degrees (alongside top impact openings)

Gamma, Theta, Α, Ζ, and W Determinationsβ2 < 5 degrees (alongside bottom impact openings)

ψ 0 degrees Ζ < 0.32 cm (Αsinψ)

Α 2.35 cm W < 0.08 cm (Asinο)

Ζ 0.000 cm Α distance between tips

ο angle of plane on side of pitots

ο 0.6 degrees ψ angle between tips

W 0.025 cm

Comments:

Calibrated by: RJN

details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems:

Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.

REMOVABLE

Pass

NOTES

All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, 

Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement

Pass

Pass (α1 measured across top impact openings)

Pass (α2 measured across bottom impact openings)

Shared Resource

#REF!

Pass

Pass

PITOT TUBE CALIBRATION

DATA SHEET

PT11

08/04/2009
Pitot Tube ID #

Calibration Date Operating Quarter/Year: 3/09

Openings Damaged? ___ Y ___N Repaired? ____Y ___ N ___ N/A

Labworks #:

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 0.3 degrees Dt 0.48 < Dt > 0.95 cm

α 2 0 degrees α < 10 degrees

β 1 0 degrees

β 2 0 degrees

β1 < 5 degrees (alongside top impact openings)

Gamma, Theta, Α, Ζ, and W Determinationsβ2 < 5 degrees (alongside bottom impact openings)

ψ 0.1 degrees Ζ < 0.32 cm (Αsinψ)

Α 2.26 cm W < 0.08 cm (Asinο)

Ζ 0.004 cm Α distance between tips

ο angle of plane on side of pitots

ο 0.8 degrees ψ angle between tips

W 0.032 cm

Comments:

Calibrated by:

PITOT TUBE CALIBRATION

DATA SHEET

PT12

08/04/2009 Shared Resource

Pass

Pass

Pass (α1 measured across top impact openings)

Pass (α2 measured across bottom impact openings)

Pass

Pass

NOTES

All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, 

Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement

details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems:

Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.

REMOVABLE

RJN
Air Services Group

Blue Team

Instrument Number:

Calibration Date:

Calibration Personnel:

Labworks #:

Difference

Time "Hg

10:05 0.01

11:07 0

12:10 -0.01

Average Difference: 0

Note: Barometric readings must agree within ± 0.1 "Hg.

Current Reference is National Weather Service, TIA.

Comments (Note any adjustments):

Current Conditions at Tampa International Airport

30.11 30.12

30.10 30.09

30.11 30.11

Barometer Reading Reference Reading

Inches Mercury Inches Mercury

BAROMETER CALIBRATION

^BR06

08/07/2009

SEG
APPENDIX B 

TURBINE DATA 
Plant Information Database Query

Plant Information Source: polk-1pisrv

Start Time: 08/27/2009 8:47

End Time: 08/27/2009 18:35

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 170.0800835 6529.01782 80.8572231 0.27653345

27-Aug-09 08:47:00 170.5224762 6545.80859 78.9909134 0.27560338

27-Aug-09 08:48:00 170.0342102 6534.49072 78.9317551 0.27562886

27-Aug-09 08:49:00 170.3021851 6548.9834 78.46978 0.27565435

27-Aug-09 08:50:00 170.8650208 6557.11475 78.6237717 0.27567983

27-Aug-09 08:51:00 170.7047882 6552.53125 78.7777634 0.27570531

27-Aug-09 08:52:00 170.1927948 6558.82568 78.9317551 0.27573079

27-Aug-09 08:53:00 170.2024384 6551.73633 79.0248108 0.27575627

27-Aug-09 08:54:00 170.4185791 6549.90332 78.7676239 0.27578175

27-Aug-09 08:55:00 170.956192 6571.29297 78.9228897 0.27580723

27-Aug-09 08:56:00 171.0022736 6558.09277 78.7589264 0.27583271

27-Aug-09 08:57:00 169.8847809 6523.62451 78.8613052 0.27585819

27-Aug-09 08:58:00 169.1328278 6509.07959 78.9636917 0.27588367

27-Aug-09 08:59:00 169.5056915 6504.49609 79.0660706 0.27590916

27-Aug-09 09:00:00 170.3726501 6524.96875 79.168457 0.27593464

27-Aug-09 09:01:00 169.756073 6499.5459 79.2708359 0.27596012

27-Aug-09 09:02:00 169.0185242 6498.32373 79.3732224 0.2759856

27-Aug-09 09:03:00 169.5222778 6523.80811 79.6308517 0.27601108

27-Aug-09 09:04:00 169.5581055 6515.19092 79.4142761 0.27603656

27-Aug-09 09:05:00 169.5939331 6514.21289 79.5132599 0.27606204

27-Aug-09 09:06:00 170.095871 6543.91406 79.6660004 0.27608752

27-Aug-09 09:07:00 170.6277618 6529.00244 79.4348068 0.276113

27-Aug-09 09:08:00 170.1584625 6524.35791 79.6243515 0.27613848

27-Aug-09 09:09:00 169.5267334 6516.04639 79.9255905 0.27616397

27-Aug-09 09:10:00 169.0944977 6510.17969 79.7624893 0.27618945

27-Aug-09 09:11:00 168.9771271 6511.09619 79.9206085 0.27621493

27-Aug-09 09:12:00 169.0254669 6521.72314 79.8202515 0.27624041

27-Aug-09 09:13:00 169.7894135 6556.41895 79.7198944 0.27626589

27-Aug-09 09:14:00 171.0684662 6556.13672 80.1036758 0.27629137

27-Aug-09 09:15:00 171.6353607 6551.61426 80.2576675 0.27631685

27-Aug-09 09:16:00 171.1860962 6545.01416 80.4116592 0.27634233

27-Aug-09 09:17:00 170.6072388 6528.88037 80.5656509 0.27636781

27-Aug-09 09:18:00 169.6759338 6520.08008 80.4989243 0.27639329

27-Aug-09 09:19:00 169.181488 6525.94678 80.2480698 0.27641878

27-Aug-09 09:20:00 169.8589172 6537.31396 80.1465149 0.27644426

Page 1 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 09:21:00 169.9703979 6545.74756 80.04496 0.27646974

27-Aug-09 09:22:00 169.4836273 6478.79102 80.1019669 0.27649522

27-Aug-09 09:23:00 169.0652008 6500.35254 80.3072891 0.2765207

27-Aug-09 09:24:00 170.7176208 6555.52783 80.5126114 0.27654618

27-Aug-09 09:25:00 170.2809448 6533.6792 80.6695099 0.27657166

27-Aug-09 09:26:00 170.6240387 6533.98975 80.7710648 0.27659714

27-Aug-09 09:27:00 170.0044708 6522.51855 80.8726196 0.27662262

27-Aug-09 09:28:00 171.4468079 6560.45117 80.8171768 0.2766481

27-Aug-09 09:29:00 171.0215302 6552.71436 80.6671371 0.27667359

27-Aug-09 09:30:00 169.7569733 6516.74658 80.7899323 0.27669907

27-Aug-09 09:31:00 170.8825989 6537.28955 80.9127274 0.27672455

27-Aug-09 09:32:00 169.368988 6502.0249 81.0355225 0.27675003

27-Aug-09 09:33:00 167.7615051 6480.96143 81.1583099 0.27677551

27-Aug-09 09:34:00 169.9698029 6540.80859 81.2483597 0.27680099

27-Aug-09 09:35:00 170.5096741 6555.28125 81.2483597 0.2768265

27-Aug-09 09:36:00 170.2611237 6528.9292 81.6088715 0.27685198

27-Aug-09 09:37:00 171.2545471 6558.93311 81.8119736 0.27687746

27-Aug-09 09:38:00 170.4933319 6540.2959 82.0150833 0.27690294

27-Aug-09 09:39:00 170.4290771 6515.3623 82.1411438 0.27692842

27-Aug-09 09:40:00 170.7388763 6550.84668 81.8306046 0.27695391

27-Aug-09 09:41:00 169.9107513 6530.18164 81.6436081 0.27697939

27-Aug-09 09:42:00 169.2546844 6501.21387 82.2595825 0.27700487

27-Aug-09 09:43:00 168.7638855 6573.52539 82.5180435 0.27703035

27-Aug-09 09:44:00 169.3734894 6496.00146 82.7244949 0.27705583

27-Aug-09 09:45:00 169.9159088 6502.12793 82.930954 0.27708131

27-Aug-09 09:46:00 170.2431183 6527.24561 82.8035202 0.27710679

27-Aug-09 09:47:00 170.5703125 6548.19238 82.7095871 0.27713227

27-Aug-09 09:48:00 171.2966003 6526.34424 82.8139572 0.27715775

27-Aug-09 09:49:00 171.0566101 6536.81445 83.4094009 0.27718323

27-Aug-09 09:50:00 170.1865997 6526.56787 83.3426743 0.27720872

27-Aug-09 09:51:00 169.4387665 6492.854 83.2400131 0.2772342

27-Aug-09 09:52:00 169.2298431 6478.37012 83.137352 0.27725968

27-Aug-09 09:53:00 169.6777191 6485.60547 83.4042664 0.27728516

27-Aug-09 09:54:00 170.1964111 6555.73682 83.7533188 0.27731064

27-Aug-09 09:55:00 170.40979 6533.55273 83.3529358 0.27733612

27-Aug-09 09:56:00 169.8905182 6509.45264 83.2502747 0.2773616

27-Aug-09 09:57:00 169.8225555 6495.43896 83.1476135 0.27738708

27-Aug-09 09:58:00 170.2397461 6544.74561 83.4402008 0.27741256

27-Aug-09 09:59:00 169.8345642 6517.43408 83.5171967 0.27743804

27-Aug-09 10:00:00 170.5185089 6534.90625 83.9021759 0.27746353

Page 2 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 10:01:00 171.1015778 6534.36377 84.1753387 0.27748901

27-Aug-09 10:02:00 169.8465881 6521.60742 84.3238297 0.27751449

27-Aug-09 10:03:00 168.8244629 6514.77539 84.1628342 0.27753997

27-Aug-09 10:04:00 168.8739929 6522.40234 84.3046799 0.27756545

27-Aug-09 10:05:00 169.1626129 6497.54102 84.2054138 0.27759093

27-Aug-09 10:06:00 169.3180084 6490.57422 84.1061401 0.27761641

27-Aug-09 10:07:00 169.373291 6493.58496 84.2460938 0.27764189

27-Aug-09 10:08:00 170.2609253 6526.21582 84.5043182 0.27766737

27-Aug-09 10:09:00 169.7085571 6516.54492 84.4005203 0.27769285

27-Aug-09 10:10:00 169.8931732 6522.59473 84.6025162 0.27771834

27-Aug-09 10:11:00 170.3612366 6530.39258 84.4497757 0.27774382

27-Aug-09 10:12:00 170.4580536 6545.97656 84.4452896 0.2777693

27-Aug-09 10:13:00 170.7708435 6557.22461 84.5992813 0.27779478

27-Aug-09 10:14:00 170.3340302 6544.11572 84.4106445 0.27782026

27-Aug-09 10:15:00 170.1284485 6519.50586 84.1546555 0.27784574

27-Aug-09 10:16:00 170.148056 6540.22656 84.3582458 0.27787122

27-Aug-09 10:17:00 170.7887573 6522.89111 84.5618286 0.2778967

27-Aug-09 10:18:00 170.7462769 6541.27441 84.8790359 0.27792218

27-Aug-09 10:19:00 169.2931976 6504.15381 84.5710526 0.27794766

27-Aug-09 10:20:00 169.6741791 6527.43799 84.532547 0.27797315

27-Aug-09 10:21:00 171.3950043 6544.5498 84.9945297 0.27799863

27-Aug-09 10:22:00 169.0497437 6482.29932 85.3425522 0.27802414

27-Aug-09 10:23:00 169.6987457 6518.78418 85.4446564 0.27804962

27-Aug-09 10:24:00 170.9640808 6552.09131 85.5467606 0.2780751

27-Aug-09 10:25:00 170.7471008 6540.90771 85.2739868 0.27810058

27-Aug-09 10:26:00 170.3076324 6528.15918 85.1187286 0.27812606

27-Aug-09 10:27:00 169.1798706 6493.50781 85.2178192 0.27815154

27-Aug-09 10:28:00 169.1698914 6464.56445 84.7558441 0.27817702

27-Aug-09 10:29:00 169.2706146 6515.53271 84.3708572 0.2782025

27-Aug-09 10:30:00 170.1027222 6561.27002 84.7748871 0.27822798

27-Aug-09 10:31:00 169.7344818 6535.26025 85.2921066 0.27825347

27-Aug-09 10:32:00 171.1630249 6533.01172 85.1368408 0.27827895

27-Aug-09 10:33:00 170.8136139 6567.79736 85.3016663 0.27830443

27-Aug-09 10:34:00 170.492569 6549.41406 85.1990051 0.27832991

27-Aug-09 10:35:00 170.6349182 6503.00293 85.096344 0.27835539

27-Aug-09 10:36:00 169.9285889 6480.76563 85.3102188 0.27838087

27-Aug-09 10:37:00 170.2747955 6512.79395 85.6233368 0.27840635

27-Aug-09 10:38:00 169.989624 6508.24854 85.7645035 0.27843183

27-Aug-09 10:39:00 170.2254944 6542.42334 86.2264786 0.27845731

27-Aug-09 10:40:00 170.913269 6541.68994 85.9521179 0.27848279

Page 3 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 10:41:00 170.5401764 6544.84326 86.2495804 0.27850828

27-Aug-09 10:42:00 170.1917419 6556.65039 87.1263199 0.27853376

27-Aug-09 10:43:00 169.6205444 6525.42041 86.769722 0.27855924

27-Aug-09 10:44:00 169.0826111 6475.10059 86.3039246 0.27858472

27-Aug-09 10:45:00 169.0826111 6504.6792 86.1226349 0.2786102

27-Aug-09 10:46:00 169.2366943 6512.37939 85.6148758 0.27863568

27-Aug-09 10:47:00 169.5448456 6509.87402 85.1071167 0.27866116

27-Aug-09 10:48:00 170.2787781 6529.4917 84.9971008 0.27868664

27-Aug-09 10:49:00 170.4257202 6526.43604 84.5145874 0.27871212

27-Aug-09 10:50:00 169.9334259 6498.93457 84.7279663 0.2787376

27-Aug-09 10:51:00 169.4411316 6504.25146 85.1937714 0.27876309

27-Aug-09 10:52:00 169.5142822 6491.60107 85.0753784 0.27878857

27-Aug-09 10:53:00 169.2260437 6496.6123 85.1972885 0.27881405

27-Aug-09 10:54:00 169.6086121 6514.94629 85.0432968 0.27883953

27-Aug-09 10:55:00 169.9716187 6500.8291 85.2092133 0.27886501

27-Aug-09 10:56:00 170.3589935 6509.81299 84.8995743 0.27889049

27-Aug-09 10:57:00 170.3140259 6514.51855 84.6839828 0.27891597

27-Aug-09 10:58:00 169.7074738 6510.66846 84.9971008 0.27894145

27-Aug-09 10:59:00 170.3447266 6515.31299 85.053566 0.27896693

27-Aug-09 11:00:00 170.6869354 6529.49121 85.3996811 0.27899241

27-Aug-09 11:01:00 170.3101959 6528.75781 85.5530472 0.2790179

27-Aug-09 11:02:00 170.745697 6516.33643 85.7064133 0.27904338

27-Aug-09 11:03:00 169.3813629 6498.97119 85.8597794 0.27906886

27-Aug-09 11:04:00 168.2611389 6500.43799 86.2444458 0.27909434

27-Aug-09 11:05:00 168.9891205 6490.50098 86.4888763 0.27911982

27-Aug-09 11:06:00 169.685379 6490.25684 86.3361359 0.2791453

27-Aug-09 11:07:00 169.8771973 6473.14502 86.3380737 0.27917078

27-Aug-09 11:08:00 168.9958649 6511.27979 86.5422821 0.27919626

27-Aug-09 11:09:00 169.6953583 6533.31299 86.7464905 0.27922174

27-Aug-09 11:10:00 170.2044983 6523.14453 86.9327545 0.27924725

27-Aug-09 11:11:00 170.7136383 6517.04834 87.0880203 0.27927274

27-Aug-09 11:12:00 170.2698059 6510.30176 87.0811462 0.27929822

27-Aug-09 11:13:00 169.7931213 6500.36475 86.979332 0.2793237

27-Aug-09 11:14:00 168.8777466 6520.66064 87.2898636 0.27934918

27-Aug-09 11:15:00 170.7681427 6545.7417 87.3101501 0.27937466

27-Aug-09 11:16:00 170.4526978 6527.16895 86.9194565 0.27940014

27-Aug-09 11:17:00 170.1081848 6489.64551 87.0734482 0.27942562

27-Aug-09 11:18:00 170.1647491 6501.13477 87.2274399 0.2794511

27-Aug-09 11:19:00 170.2853394 6496.73486 87.3814316 0.27947658

27-Aug-09 11:20:00 169.1207428 6488.42334 87.1278458 0.27950206

Page 4 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 11:21:00 169.4689484 6485.53369 86.8223572 0.27952754

27-Aug-09 11:22:00 169.6340485 6509.13232 86.655098 0.27955303

27-Aug-09 11:23:00 170.1660919 6532.73096 87.1786728 0.27957851

27-Aug-09 11:24:00 170.1214294 6535.69873 87.1016769 0.27960399

27-Aug-09 11:25:00 170.3387604 6516.90186 87.0246811 0.27962947

27-Aug-09 11:26:00 169.9885101 6513.11279 86.9476852 0.27965495

27-Aug-09 11:27:00 169.7198181 6490.37891 86.9168854 0.27968043

27-Aug-09 11:28:00 169.4511261 6491.73779 87.4918518 0.27970591

27-Aug-09 11:29:00 169.403656 6495.68994 87.2876434 0.27973139

27-Aug-09 11:30:00 170.1892548 6526.05078 87.0834351 0.27975687

27-Aug-09 11:31:00 170.4193115 6512.37402 86.8792267 0.27978235

27-Aug-09 11:32:00 169.0139465 6469.82031 87.1786728 0.27980784

27-Aug-09 11:33:00 168.1738129 6515.58203 87.0902405 0.27983332

27-Aug-09 11:34:00 168.9933167 6510.48535 86.9881363 0.2798588

27-Aug-09 11:35:00 170.2270508 6543.25342 86.8860321 0.27988428

27-Aug-09 11:36:00 170.7331696 6555.4707 87.1576309 0.27990976

27-Aug-09 11:37:00 170.5620575 6552.90381 86.6081543 0.27993524

27-Aug-09 11:38:00 170.2055969 6544.60498 86.8288574 0.27996072

27-Aug-09 11:39:00 169.60672 6498.33545 86.3060455 0.2799862

27-Aug-09 11:40:00 168.8327484 6496.28271 86.5052948 0.28001168

27-Aug-09 11:41:00 169.0710449 6521.31445 86.3069839 0.28003716

27-Aug-09 11:42:00 170.9378815 6568.24316 86.3163071 0.28006265

27-Aug-09 11:43:00 171.0399475 6565.15234 86.4869461 0.28008813

27-Aug-09 11:44:00 170.2267609 6557.37402 86.327858 0.28011361

27-Aug-09 11:45:00 170.1571198 6516.13867 86.4805679 0.28013909

27-Aug-09 11:46:00 169.5567474 6537.36279 86.1109848 0.28016457

27-Aug-09 11:47:00 169.7697296 6529.22217 86.1608658 0.28019005

27-Aug-09 11:48:00 170.4747162 6550.89355 86.4549026 0.28021553

27-Aug-09 11:49:00 170.5673218 6547.81152 86.3009109 0.28024101

27-Aug-09 11:50:00 169.6325378 6529.6748 86.5550613 0.28026649

27-Aug-09 11:51:00 170.00177 6542.1416 87.0132904 0.28029197

27-Aug-09 11:52:00 170.3709869 6556.96143 87.188942 0.28031746

27-Aug-09 11:53:00 170.8801422 6588.40479 87.188942 0.28034294

27-Aug-09 11:54:00 170.0361328 6523.38037 87.5379944 0.28036842

27-Aug-09 11:55:00 169.7425537 6520.59912 87.6443863 0.2803939

27-Aug-09 11:56:00 170.8079987 6550.42285 87.3338547 0.28041938

27-Aug-09 11:57:00 170.3863068 6559.77295 87.4225006 0.28044486

27-Aug-09 11:58:00 169.3957367 6510.58838 87.2685013 0.28047037

27-Aug-09 11:59:00 169.1375427 6505.22656 87.3428497 0.28049585

27-Aug-09 12:00:00 169.1375427 6503.84814 87.188942 0.28052133

Page 5 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 12:01:00 170.2178955 6533.65918 87.5020599 0.28054681

27-Aug-09 12:02:00 170.9772186 6526.06934 87.23069 0.2805723

27-Aug-09 12:03:00 171.321106 6556.96191 87.1252975 0.28059778

27-Aug-09 12:04:00 170.3847809 6568.87891 86.9725571 0.28062326

27-Aug-09 12:05:00 171.1953735 6576.43066 86.9896851 0.28064874

27-Aug-09 12:06:00 169.7220001 6545.90039 87.3002167 0.28067422

27-Aug-09 12:07:00 169.6167908 6527.2915 87.1371841 0.2806997

27-Aug-09 12:08:00 168.9642029 6498.59863 86.9819183 0.28072518

27-Aug-09 12:09:00 169.3428497 6523.25879 87.0980377 0.28075066

27-Aug-09 12:10:00 169.896637 6524.73779 87.0400848 0.28077614

27-Aug-09 12:11:00 169.9685059 6524.16211 87.5213089 0.28080162

27-Aug-09 12:12:00 169.9321899 6508.65186 87.5983047 0.28082711

27-Aug-09 12:13:00 169.4923248 6525.15234 87.6753006 0.28085259

27-Aug-09 12:14:00 169.5792694 6541.65283 87.7522964 0.28087807

27-Aug-09 12:15:00 170.9722595 6556.35693 88.1098251 0.28090355

27-Aug-09 12:16:00 171.3225708 6553.34131 87.9866257 0.28092903

27-Aug-09 12:17:00 170.6003265 6533.95264 87.8634338 0.28095451

27-Aug-09 12:18:00 169.6727753 6495.6958 87.7402344 0.28097999

27-Aug-09 12:19:00 169.2330017 6540.06396 87.6170425 0.28100547

27-Aug-09 12:20:00 169.5571899 6533.74805 87.8074799 0.28103095

27-Aug-09 12:21:00 170.0888214 6546.68945 87.6534882 0.28105643

27-Aug-09 12:22:00 170.7587433 6562.00391 87.4917908 0.28108191

27-Aug-09 12:23:00 170.9809723 6592.38672 86.875824 0.2811074

27-Aug-09 12:24:00 170.8368835 6566.2041 87.3340454 0.28113288

27-Aug-09 12:25:00 170.085144 6538.62793 87.7922668 0.28115836

27-Aug-09 12:26:00 169.1201477 6499.48438 87.8151779 0.28118384

27-Aug-09 12:27:00 169.1070251 6502.67773 87.8151779 0.28120932

27-Aug-09 12:28:00 169.4218292 6516.79492 87.8151779 0.2812348

27-Aug-09 12:29:00 169.8513794 6529.52197 87.9135132 0.28126028

27-Aug-09 12:30:00 169.6997223 6529.68604 88.3793182 0.28128576

27-Aug-09 12:31:00 169.8138428 6557.73584 87.9075775 0.28131124

27-Aug-09 12:32:00 170.7141266 6564.29541 88.0748367 0.28133672

27-Aug-09 12:33:00 170.9615631 6547.79492 88.3803253 0.28136221

27-Aug-09 12:34:00 170.2323151 6532.25342 88.068779 0.28138769

27-Aug-09 12:35:00 170.3313751 6527.26172 87.6029816 0.28141317

27-Aug-09 12:36:00 169.6642151 6523.35547 87.3350601 0.28143865

27-Aug-09 12:37:00 169.8871002 6525.33545 87.3660355 0.28146413

27-Aug-09 12:38:00 169.0766144 6495.63477 87.597023 0.28148961

27-Aug-09 12:39:00 168.6212311 6498.31152 87.8280182 0.28151509

27-Aug-09 12:40:00 169.5686188 6525.0791 88.0590057 0.28154057

Page 6 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 12:41:00 170.6591339 6548.3042 88.4414215 0.28156605

27-Aug-09 12:42:00 170.373703 6541.84863 88.077179 0.28159153

27-Aug-09 12:43:00 170.6183014 6559.59717 88.0004959 0.28161702

27-Aug-09 12:44:00 170.9653015 6573.70068 87.9238129 0.2816425

27-Aug-09 12:45:00 170.6999054 6555 87.8471298 0.28166798

27-Aug-09 12:46:00 169.7997589 6536.29932 88.1283035 0.28168392

27-Aug-09 12:47:00 169.5701141 6520.81787 87.8998795 0.28167754

27-Aug-09 12:48:00 169.3605804 6534.31006 88.0538712 0.28167117

27-Aug-09 12:49:00 169.734314 6547.80273 88.0966873 0.28166482

27-Aug-09 12:50:00 170.1080322 6558.45898 88.0354843 0.28165844

27-Aug-09 12:51:00 169.4612427 6540.08301 87.9742889 0.28165206

27-Aug-09 12:52:00 169.4440002 6545.44482 87.9130936 0.28164569

27-Aug-09 12:53:00 169.4484711 6550.10645 87.8518982 0.28163931

27-Aug-09 12:54:00 168.4985809 6548.46973 87.8767776 0.28163296

27-Aug-09 12:55:00 170.0142975 6548.95605 88.0307693 0.28162658

27-Aug-09 12:56:00 170.4215088 6571.59863 88.0153732 0.2816202

27-Aug-09 12:57:00 170.2444611 6573.0376 87.9212341 0.28161383

27-Aug-09 12:58:00 169.1786041 6506.5127 88.0787277 0.28160748

27-Aug-09 12:59:00 169.3507233 6537.55859 87.9221649 0.2816011

27-Aug-09 13:00:00 169.3125763 6532.11914 88.1591034 0.28159472

27-Aug-09 13:01:00 169.5561981 6543.2417 88.2617645 0.28158835

27-Aug-09 13:02:00 170.7547455 6567.07617 88.3644257 0.281582

27-Aug-09 13:03:00 170.8305054 6572.6377 88.1283035 0.28157562

27-Aug-09 13:04:00 170.5957184 6583.57666 88.1283035 0.28156924

27-Aug-09 13:05:00 169.9676971 6544.15869 88.1283035 0.28156286

27-Aug-09 13:06:00 170.5710602 6576.18213 87.9383698 0.28155649

27-Aug-09 13:07:00 170.2480316 6566.64844 88.3858719 0.28155014

27-Aug-09 13:08:00 169.5722198 6549.96436 88.1515961 0.28154376

27-Aug-09 13:09:00 169.616333 6521.19775 88.3068619 0.28153738

27-Aug-09 13:10:00 169.9675446 6580.8877 88.1648331 0.28153101

27-Aug-09 13:11:00 170.5402985 6552.93018 88.0969925 0.28152466

27-Aug-09 13:12:00 170.1680756 6559.61523 88.1155243 0.28151828

27-Aug-09 13:13:00 170.0981293 6566.30078 87.9621582 0.2815119

27-Aug-09 13:14:00 169.8063507 6560.17676 87.8087921 0.28150553

27-Aug-09 13:15:00 170.0473938 6524.02783 87.655426 0.28149918

27-Aug-09 13:16:00 170.2545319 6537.91064 87.5020599 0.2814928

27-Aug-09 13:17:00 169.7052002 6519.79248 88.112648 0.28148642

27-Aug-09 13:18:00 168.9416199 6506.52588 87.9144211 0.28148004

27-Aug-09 13:19:00 169.2804413 6509.19971 88.0170822 0.28147367

27-Aug-09 13:20:00 169.377243 6511.87402 88.119751 0.28146732

Page 7 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 13:21:00 169.1670837 6513.17432 88.3683624 0.28146094

27-Aug-09 13:22:00 169.6386566 6517.84912 88.0299683 0.28145456

27-Aug-09 13:23:00 170.2182007 6530.59766 87.5641632 0.28144819

27-Aug-09 13:24:00 169.6958771 6484.50537 87.6431351 0.28144184

27-Aug-09 13:25:00 170.1439056 6514.37207 87.4366837 0.28143546

27-Aug-09 13:26:00 170.3150177 6544.23926 87.2302322 0.28142908

27-Aug-09 13:27:00 170.6189423 6559.71289 87.5020599 0.2814227

27-Aug-09 13:28:00 170.2001953 6527.89355 87.9537735 0.28141636

27-Aug-09 13:29:00 169.5707092 6505.31201 88.1283035 0.28140998

27-Aug-09 13:30:00 169.898056 6516.12891 88.0359039 0.2814036

27-Aug-09 13:31:00 170.121994 6523.80811 88.4414215 0.28139722

27-Aug-09 13:32:00 169.7880554 6522.73828 88.8880539 0.28139085

27-Aug-09 13:33:00 169.9006195 6531.05762 88.8061523 0.2813845

27-Aug-09 13:34:00 170.3186188 6531.28418 88.3101654 0.28137812

27-Aug-09 13:35:00 169.715271 6504.91992 88.2266388 0.28137174

27-Aug-09 13:36:00 169.0798187 6493.64209 88.3819046 0.28136536

27-Aug-09 13:37:00 169.2659454 6522.53027 88.0366592 0.28135902

27-Aug-09 13:38:00 170.1712341 6509.36084 87.8839111 0.28135264

27-Aug-09 13:39:00 170.1598053 6528.59912 88.1596146 0.28134626

27-Aug-09 13:40:00 170.5200348 6535.19922 88.3846436 0.28133988

27-Aug-09 13:41:00 171.5646667 6536.81494 88.2814178 0.28133354

27-Aug-09 13:42:00 170.3069153 6533.64746 88.1781921 0.28132716

27-Aug-09 13:43:00 170.5548859 6566.53809 88.197464 0.28132078

27-Aug-09 13:44:00 169.7204437 6541.48975 88.3313141 0.2813144

27-Aug-09 13:45:00 168.5708008 6505.20508 88.4651718 0.28130803

27-Aug-09 13:46:00 169.210495 6500.76221 88.5990219 0.28130168

27-Aug-09 13:47:00 170.7658844 6540.80469 88.7328796 0.2812953

27-Aug-09 13:48:00 170.79245 6567.6001 88.8154221 0.28128892

27-Aug-09 13:49:00 170.921524 6547.32422 88.4414215 0.28128254

27-Aug-09 13:50:00 171.1286469 6544.95898 88.1552505 0.2812762

27-Aug-09 13:51:00 170.7000885 6549.19434 88.2322464 0.28126982

27-Aug-09 13:52:00 169.063858 6527.71924 88.3092422 0.28126344

27-Aug-09 13:53:00 169.2663269 6513.85596 88.3862381 0.28125706

27-Aug-09 13:54:00 169.3860168 6511.88965 88.4121704 0.28125072

27-Aug-09 13:55:00 169.7327423 6509.92285 88.3089447 0.28124434

27-Aug-09 13:56:00 170.5871277 6537.76611 88.205719 0.28123796

27-Aug-09 13:57:00 170.614151 6542.92383 87.9666901 0.28123158

27-Aug-09 13:58:00 171.0965271 6547.71533 88.4190521 0.2812252

27-Aug-09 13:59:00 170.1565094 6536.33887 88.3158264 0.28121886

27-Aug-09 14:00:00 169.3514252 6507.97461 88.2126007 0.28121248

Page 8 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 14:01:00 169.4527283 6513.6084 88.4414215 0.2812061

27-Aug-09 14:02:00 168.9928589 6508.71875 88.1490021 0.28119972

27-Aug-09 14:03:00 169.1873169 6534.34961 88.3042679 0.28119338

27-Aug-09 14:04:00 170.1629639 6556.13672 88.4057846 0.281187

27-Aug-09 14:05:00 170.4044189 6539.58008 88.100296 0.28118062

27-Aug-09 14:06:00 170.2409821 6539.10107 87.8357086 0.28117424

27-Aug-09 14:07:00 170.3715973 6523.38428 88.1180954 0.28116786

27-Aug-09 14:08:00 169.5587006 6514.61621 87.9138794 0.28116152

27-Aug-09 14:09:00 169.2099762 6499.7168 87.709671 0.28115514

27-Aug-09 14:10:00 169.9111633 6570.82275 87.5054626 0.28114876

27-Aug-09 14:11:00 170.4022369 6564.03271 87.8049088 0.28114238

27-Aug-09 14:12:00 170.3559875 6553.74463 87.5174561 0.28113604

27-Aug-09 14:13:00 170.6431885 6550.89355 87.7995224 0.28112966

27-Aug-09 14:14:00 170.1712036 6532.30273 87.5020599 0.28112328

27-Aug-09 14:15:00 170.0391541 6533.99707 87.5020599 0.2811169

27-Aug-09 14:16:00 170.1460114 6522.53467 87.5467911 0.28111055

27-Aug-09 14:17:00 169.8871002 6522.1333 87.7638474 0.28110418

27-Aug-09 14:18:00 170.8066559 6545.60107 87.554245 0.2810978

27-Aug-09 14:19:00 170.56604 6555.70654 87.5636597 0.28109142

27-Aug-09 14:20:00 170.5717621 6536.97852 87.2556686 0.28108504

27-Aug-09 14:21:00 169.7053375 6521.77881 87.4301987 0.2810787

27-Aug-09 14:22:00 169.0015564 6521.65771 88.0193939 0.28107232

27-Aug-09 14:23:00 169.355011 6540.125 88.0914688 0.28106594

27-Aug-09 14:24:00 169.7084503 6560.18896 88.0300674 0.28105956

27-Aug-09 14:25:00 169.9757233 6530.85986 87.9686737 0.28105322

27-Aug-09 14:26:00 170.2415314 6529.13281 87.9072723 0.28104684

27-Aug-09 14:27:00 169.3237 6499.87012 87.8458786 0.28104046

27-Aug-09 14:28:00 170.6329041 6520.31494 87.931076 0.28103408

27-Aug-09 14:29:00 170.6092987 6528.93213 88.1628799 0.28102773

27-Aug-09 14:30:00 170.0906219 6532.93604 88.3946838 0.28102136

27-Aug-09 14:31:00 170.4086914 6516.38965 88.6264877 0.28101498

27-Aug-09 14:32:00 169.8900757 6505.02441 88.8582916 0.2810086

27-Aug-09 14:33:00 170.1629639 6519.56055 89.0900955 0.28100222

27-Aug-09 14:34:00 170.1530609 6538.09619 89.3218994 0.28099588

27-Aug-09 14:35:00 170.7651367 6542.53271 89.4416656 0.2809895

27-Aug-09 14:36:00 170.3517303 6513.52832 88.9899445 0.28098312

27-Aug-09 14:37:00 169.7666779 6525.26221 88.4414215 0.28097674

27-Aug-09 14:38:00 169.8653259 6524.35986 88.9009781 0.28097039

27-Aug-09 14:39:00 170.1174927 6536.10352 89.1063004 0.28096402

27-Aug-09 14:40:00 170.1582336 6532.93213 89.3116226 0.28095764

Page 9 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 14:41:00 169.1375427 6524.49854 89.2158051 0.28095126

27-Aug-09 14:42:00 169.0284271 6510.02686 88.4056854 0.28094491

27-Aug-09 14:43:00 169.8744965 6507.02588 88.3035812 0.28093854

27-Aug-09 14:44:00 170.7363129 6539.5249 88.2014771 0.28093216

27-Aug-09 14:45:00 170.7369843 6534.54102 88.0993729 0.28092578

27-Aug-09 14:46:00 170.2371826 6529.55762 87.9972687 0.2809194

27-Aug-09 14:47:00 170.5987549 6530.68896 87.8951569 0.28091305

27-Aug-09 14:48:00 170.5061951 6536.73926 87.8819122 0.28090668

27-Aug-09 14:49:00 170.4136505 6526.67578 88.1898956 0.2809003

27-Aug-09 14:50:00 170.5191498 6522.14551 88.3840179 0.28089392

27-Aug-09 14:51:00 170.2019958 6504.90576 88.3900909 0.28088757

27-Aug-09 14:52:00 169.3824921 6513.6875 88.0820999 0.2808812

27-Aug-09 14:53:00 170.2154999 6533.23584 87.8973083 0.28087482

27-Aug-09 14:54:00 170.9555969 6526.17725 88.4414215 0.28086844

27-Aug-09 14:55:00 170.5743866 6519.11914 88.4977417 0.28086209

27-Aug-09 14:56:00 170.2612457 6512.06055 89.1387329 0.28085572

27-Aug-09 14:57:00 169.3123932 6499.93701 89.2914734 0.28084934

27-Aug-09 14:58:00 169.4373169 6494.32666 89.4334641 0.28084296

27-Aug-09 14:59:00 170.6268463 6526.68652 88.9415436 0.28083658

27-Aug-09 15:00:00 170.2242126 6522.62207 88.4496231 0.28083023

27-Aug-09 15:01:00 170.0591125 6503.07813 88.6222916 0.28082386

27-Aug-09 15:02:00 169.8940125 6507.63135 88.8062286 0.28081748

27-Aug-09 15:03:00 170.0867767 6549.86816 88.9087524 0.2808111

27-Aug-09 15:04:00 170.628067 6570.37646 89.4006729 0.28080475

27-Aug-09 15:05:00 169.196167 6497.95264 89.1994095 0.28079838

27-Aug-09 15:06:00 168.4592743 6476.16406 89.1285477 0.280792

27-Aug-09 15:07:00 169.624588 6527.13037 89.1285477 0.28078562

27-Aug-09 15:08:00 170.5770721 6546.87842 89.6347275 0.28077927

27-Aug-09 15:09:00 170.6736145 6523.4292 89.4968948 0.28077289

27-Aug-09 15:10:00 170.0319366 6527.8291 89.1917572 0.28076652

27-Aug-09 15:11:00 170.0206909 6524.07666 88.8866196 0.28076014

27-Aug-09 15:12:00 170.4295349 6517.63525 88.4414215 0.28075376

27-Aug-09 15:13:00 169.4772034 6517.63525 88.4808502 0.28074741

27-Aug-09 15:14:00 170.884491 6523.48389 88.9727707 0.28074104

27-Aug-09 15:15:00 170.2917633 6519.45654 88.9180832 0.28073466

27-Aug-09 15:16:00 168.9645081 6508.29102 89.1785965 0.28072828

27-Aug-09 15:17:00 169.5514679 6507.92432 89.2555923 0.28072193

27-Aug-09 15:18:00 169.1173096 6497.10107 89.3325882 0.28071555

27-Aug-09 15:19:00 169.72995 6506.47021 89.409584 0.28070918

27-Aug-09 15:20:00 170.3603363 6520.12891 89.1285477 0.2807028

Page 10 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 15:21:00 169.6525421 6495.79346 88.5874329 0.28069645

27-Aug-09 15:22:00 170.0278778 6504.66699 88.1283035 0.28069007

27-Aug-09 15:23:00 170.1638489 6540.04004 87.7102432 0.2806837

27-Aug-09 15:24:00 171.1084442 6527.35254 87.5071411 0.28067732

27-Aug-09 15:25:00 169.2849579 6512.34424 87.3040314 0.28067094

27-Aug-09 15:26:00 170.7983093 6525.22852 87.3875046 0.28066459

27-Aug-09 15:27:00 169.1186218 6538.11279 87.8457336 0.28065822

27-Aug-09 15:28:00 169.9849396 6556.64404 88.1873322 0.28065184

27-Aug-09 15:29:00 171.3356323 6545.41162 88.3413239 0.28064546

27-Aug-09 15:30:00 170.189682 6519.48096 88.2258301 0.28063911

27-Aug-09 15:31:00 169.873291 6537.71094 88.0291443 0.28063273

27-Aug-09 15:32:00 169.7135925 6525.52197 87.9897079 0.28062636

27-Aug-09 15:33:00 169.6114655 6498.01807 87.5277252 0.28061998

27-Aug-09 15:34:00 169.2197266 6494.32422 87.2598495 0.2806136

27-Aug-09 15:35:00 169.2816315 6482.33008 87.5257645 0.28060725

27-Aug-09 15:36:00 169.8203735 6492.62793 87.7916718 0.28060088

27-Aug-09 15:37:00 170.100708 6519.02881 88.057579 0.2805945

27-Aug-09 15:38:00 170.4094849 6528.55908 88.3234863 0.28058812

27-Aug-09 15:39:00 170.125824 6520.05469 88.5894012 0.28058177

27-Aug-09 15:40:00 170.3349762 6534.01611 88.9078217 0.28057539

27-Aug-09 15:41:00 170.7105255 6553.36816 89.4416656 0.28056902

27-Aug-09 15:42:00 170.4193268 6541.35352 89.3765411 0.28056264

27-Aug-09 15:43:00 170.2183075 6540.83984 88.7252884 0.28055629

27-Aug-09 15:44:00 169.89711 6535.5293 88.4310684 0.28054991

27-Aug-09 15:45:00 169.5759125 6502.45215 88.2758026 0.28054354

27-Aug-09 15:46:00 169.7078857 6510.68066 88.1751862 0.28053716

27-Aug-09 15:47:00 170.5506287 6540.46729 89.112915 0.28053078

27-Aug-09 15:48:00 170.6042175 6539.5874 89.2812271 0.28052443

27-Aug-09 15:49:00 170.6043854 6529.02686 89.4364929 0.28051805

27-Aug-09 15:50:00 170.5053253 6521.18018 89.2748413 0.28051168

27-Aug-09 15:51:00 170.3763275 6518.7417 89.428833 0.2805053

27-Aug-09 15:52:00 170.1827087 6540.62939 89.1593475 0.28049895

27-Aug-09 15:53:00 170.4589081 6574.54736 89.3595352 0.28049257

27-Aug-09 15:54:00 170.4597015 6562.65137 89.4416656 0.2804862

27-Aug-09 15:55:00 169.786377 6526.24023 89.6534576 0.28047982

27-Aug-09 15:56:00 169.417572 6515.97314 89.5664291 0.28047347

27-Aug-09 15:57:00 170.033905 6524.66943 89.7161407 0.28046709

27-Aug-09 15:58:00 170.5429993 6532.31055 88.6709824 0.28046072

27-Aug-09 15:59:00 170.4200745 6517.15479 88.2013626 0.28045434

27-Aug-09 16:00:00 169.8708801 6501.99854 88.061142 0.28044796

Page 11 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 16:01:00 169.9496918 6497.00342 88.3890915 0.28044161

27-Aug-09 16:02:00 169.0352173 6516.59521 88.717041 0.28043523

27-Aug-09 16:03:00 170.3656311 6523.20996 88.5671082 0.28042886

27-Aug-09 16:04:00 170.5749664 6530.15137 88.7510452 0.28042248

27-Aug-09 16:05:00 170.5836639 6540.55908 88.4982681 0.28041613

27-Aug-09 16:06:00 171.0915222 6529.00244 88.0103455 0.28040975

27-Aug-09 16:07:00 170.7725525 6529.00244 87.7539139 0.28040338

27-Aug-09 16:08:00 171.3074188 6526.69873 87.6518097 0.280397

27-Aug-09 16:09:00 170.2491608 6509.17139 87.5497055 0.28039065

27-Aug-09 16:10:00 169.9544067 6517.87988 87.5841904 0.28038427

27-Aug-09 16:11:00 171.2598114 6537.49121 87.7381821 0.28037789

27-Aug-09 16:12:00 170.7011871 6537.90088 88.1231689 0.28037152

27-Aug-09 16:13:00 170.1923828 6554.03467 87.8408508 0.28036514

27-Aug-09 16:14:00 169.7826385 6534.01416 87.8620224 0.28035879

27-Aug-09 16:15:00 170.0083618 6512.91748 88.6619339 0.28035241

27-Aug-09 16:16:00 170.3611908 6518.51563 89.0649033 0.28034604

27-Aug-09 16:17:00 169.5339813 6509.71533 88.9121628 0.28033966

27-Aug-09 16:18:00 169.7074127 6491.69922 88.4546814 0.28033331

27-Aug-09 16:19:00 169.6708527 6493.95996 87.8151779 0.28032693

27-Aug-09 16:20:00 170.1742249 6519.38916 87.7553635 0.28032055

27-Aug-09 16:21:00 170.52948 6525.40918 88.555275 0.28031418

27-Aug-09 16:22:00 169.8370361 6509.6665 89.0852737 0.28030783

27-Aug-09 16:23:00 169.1825867 6501.11621 88.9325256 0.28030145

27-Aug-09 16:24:00 169.1050568 6496.20313 88.8884811 0.28029507

27-Aug-09 16:25:00 169.5057983 6500.30664 89.374939 0.2802887

27-Aug-09 16:26:00 170.3030396 6533.49121 89.1688232 0.28028232

27-Aug-09 16:27:00 171.0404053 6539.1167 89.3701935 0.28027597

27-Aug-09 16:28:00 170.4250336 6522.19434 89.5715637 0.28026959

27-Aug-09 16:29:00 170.0727539 6512.66064 89.6637497 0.28026322

27-Aug-09 16:30:00 170.13974 6515.97607 89.4103546 0.28025684

27-Aug-09 16:31:00 170.545929 6533.02686 89.4416656 0.28025049

27-Aug-09 16:32:00 171.2694397 6557.07813 89.4416656 0.28024411

27-Aug-09 16:33:00 170.8819885 6509.84814 89.7440948 0.28023773

27-Aug-09 16:34:00 170.1547241 6487.95264 89.6844025 0.28023136

27-Aug-09 16:35:00 169.9307251 6514.37207 89.6247177 0.28022501

27-Aug-09 16:36:00 169.5973511 6496.97314 89.5650253 0.28021863

27-Aug-09 16:37:00 169.7999725 6495.23145 89.5053329 0.28021225

27-Aug-09 16:38:00 170.0408936 6497.77686 89.4456482 0.28020588

27-Aug-09 16:39:00 170.1095276 6519.59131 89.716629 0.2801995

27-Aug-09 16:40:00 170.2215118 6522.31543 89.3341522 0.28019315

Page 12 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 16:41:00 170.70961 6550.08643 88.8764496 0.28018677

27-Aug-09 16:42:00 169.9752045 6499.86963 87.9627533 0.28018039

27-Aug-09 16:43:00 169.4077759 6517.25049 88.3387604 0.28017402

27-Aug-09 16:44:00 170.1007538 6521.41211 88.4414215 0.28016767

27-Aug-09 16:45:00 169.3354645 6498.00293 88.0672073 0.28016129

27-Aug-09 16:46:00 169.9875183 6534.9917 87.6089783 0.28015491

27-Aug-09 16:47:00 170.4713593 6532.21045 87.4430313 0.28014854

27-Aug-09 16:48:00 170.555954 6518.89844 87.3660355 0.28014219

27-Aug-09 16:49:00 170.057373 6528.12256 87.2890396 0.28013581

27-Aug-09 16:50:00 169.5587921 6522.15479 87.2120438 0.28012943

27-Aug-09 16:51:00 169.2341156 6512.8042 87.0914154 0.28012305

27-Aug-09 16:52:00 170.3270264 6519.6792 86.7757263 0.28011668

27-Aug-09 16:53:00 169.389328 6473.02246 86.621727 0.28011033

27-Aug-09 16:54:00 169.1146545 6463.67236 86.7526245 0.28010395

27-Aug-09 16:55:00 169.439682 6485.42871 87.0691681 0.28009757

27-Aug-09 16:56:00 169.8719482 6485.48975 86.8638458 0.2800912

27-Aug-09 16:57:00 169.4355927 6480.35596 86.6585159 0.28008485

27-Aug-09 16:58:00 168.9845123 6460.23438 86.6728058 0.28007847

27-Aug-09 16:59:00 170.2840118 6504.89795 86.8792648 0.28007209

27-Aug-09 17:00:00 169.7063904 6497.83496 87.0857162 0.28006572

27-Aug-09 17:01:00 170.5477905 6522.03564 87.2653122 0.28005934

27-Aug-09 17:02:00 170.6016846 6525.39697 87.4180527 0.28005299

27-Aug-09 17:03:00 170.5386505 6537.39893 87.3634644 0.28004661

27-Aug-09 17:04:00 169.7898712 6507.64404 87.322403 0.28004023

27-Aug-09 17:05:00 169.0138702 6470.00635 87.3737335 0.28003386

27-Aug-09 17:06:00 170.1628265 6490.31787 87.5631561 0.28002751

27-Aug-09 17:07:00 170.9913177 6522.21875 87.7158966 0.28002113

27-Aug-09 17:08:00 170.6863556 6523.56348 87.7055893 0.28001475

27-Aug-09 17:09:00 170.6522064 6518.79639 87.7141724 0.28000838

27-Aug-09 17:10:00 170.5758667 6533.22852 87.6899338 0.28000203

27-Aug-09 17:11:00 169.8788452 6495.50244 88.0939331 0.27999565

27-Aug-09 17:12:00 170.4197845 6502.23486 88.8154221 0.27998927

27-Aug-09 17:13:00 170.1124573 6543.36426 88.9694138 0.27998289

27-Aug-09 17:14:00 169.6847839 6511.27979 89.0607071 0.27997652

27-Aug-09 17:15:00 169.932663 6517.39111 89.2500305 0.27997017

27-Aug-09 17:16:00 170.7321014 6517.58301 89.6911926 0.27996379

27-Aug-09 17:17:00 170.0616455 6514.43994 89.4796524 0.27995741

27-Aug-09 17:18:00 169.903717 6522.854 89.7075653 0.27995104

27-Aug-09 17:19:00 170.4977112 6533.30762 89.9354858 0.27994469

27-Aug-09 17:20:00 170.8037109 6543.76074 90.1633987 0.27993831

Page 13 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 17:21:00 170.3385773 6535.57227 90.3341827 0.27993193

27-Aug-09 17:22:00 169.9609528 6523.65527 89.8764801 0.27992555

27-Aug-09 17:23:00 170.2735748 6520.75195 89.4338989 0.27991921

27-Aug-09 17:24:00 170.5862122 6535.79541 89.2786407 0.27991283

27-Aug-09 17:25:00 170.8988342 6536.04248 89.4252701 0.27990645

27-Aug-09 17:26:00 170.7798462 6544.64111 88.4414215 0.27990007

27-Aug-09 17:27:00 170.0769043 6472.41797 88.6253586 0.2798937

27-Aug-09 17:28:00 169.2508698 6483.87012 88.809288 0.27988735

27-Aug-09 17:29:00 168.450882 6485.39844 89.4211349 0.27988097

27-Aug-09 17:30:00 169.632843 6485.03174 89.2510681 0.27987459

27-Aug-09 17:31:00 170.6422119 6508.47461 89.0468597 0.27986822

27-Aug-09 17:32:00 169.7098389 6504.76514 88.8426514 0.27986187

27-Aug-09 17:33:00 170.1916962 6497.79834 89.3492661 0.27985549

27-Aug-09 17:34:00 169.9037323 6522.94336 89.4416656 0.27984911

27-Aug-09 17:35:00 169.756073 6479.28711 89.4416656 0.27984273

27-Aug-09 17:36:00 170.1432953 6493.81152 89.4416656 0.27983639

27-Aug-09 17:37:00 170.235611 6514.22314 89.7460861 0.27983001

27-Aug-09 17:38:00 170.9166718 6534.63477 89.742363 0.27982363

27-Aug-09 17:39:00 169.8521423 6501.04297 90.1523972 0.27981725

27-Aug-09 17:40:00 170.1313019 6540.4834 90.562439 0.27981088

27-Aug-09 17:41:00 170.4380951 6528.96582 90.1583557 0.27980453

27-Aug-09 17:42:00 171.0272827 6529.18262 90.2704926 0.27979815

27-Aug-09 17:43:00 169.6585693 6511.21826 90.1177521 0.27979177

27-Aug-09 17:44:00 169.6086426 6515.28271 89.6846313 0.27978539

27-Aug-09 17:45:00 169.5587006 6480.84521 89.6213226 0.27977905

27-Aug-09 17:46:00 170.3649902 6517.98389 89.5714188 0.27977267

27-Aug-09 17:47:00 169.4240265 6476.56104 89.6086044 0.27976629

27-Aug-09 17:48:00 169.256424 6476.53076 89.5889664 0.27975991

27-Aug-09 17:49:00 169.1483459 6474.87158 89.5938721 0.27975357

27-Aug-09 17:50:00 169.7454224 6472.12109 89.1389847 0.27974719

27-Aug-09 17:51:00 169.3066101 6455.60547 89.0234146 0.27974081

27-Aug-09 17:52:00 169.3307037 6468.79785 88.7981262 0.27973443

27-Aug-09 17:53:00 170.2735901 6486.15381 88.5728378 0.27972806

27-Aug-09 17:54:00 170.3205109 6503.51025 88.8154221 0.27972171

27-Aug-09 17:55:00 170.1434479 6478.32715 89.2466049 0.27971533

27-Aug-09 17:56:00 169.8883057 6483.31738 89.3856583 0.27970895

27-Aug-09 17:57:00 170.1631927 6493.03418 89.2329178 0.27970257

27-Aug-09 17:58:00 170.6053314 6519.43213 89.2007217 0.27969623

27-Aug-09 17:59:00 170.1295929 6498.55615 89.4286346 0.27968985

27-Aug-09 18:00:00 169.6930389 6496.21631 89.6565552 0.27968347

Page 14 of 15
Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

27-Aug-09 18:01:00 170.1477051 6510.9751 89.8844681 0.27967709

27-Aug-09 18:02:00 170.2306671 6500.68115 89.8456116 0.27967075

27-Aug-09 18:03:00 170.2426605 6498.64111 89.1285477 0.27966437

27-Aug-09 18:04:00 170.2968445 6522.45996 89.1285477 0.27965799

27-Aug-09 18:05:00 170.6030273 6549.00635 89.1285477 0.27965161

27-Aug-09 18:06:00 170.4259186 6519.38965 89.0271683 0.27964523

27-Aug-09 18:07:00 169.9036102 6469.72266 88.4495926 0.27963889

27-Aug-09 18:08:00 170.6526337 6448.18604 88.51091 0.27963251

27-Aug-09 18:09:00 170.8215637 6540.79102 88.5722198 0.27962613

27-Aug-09 18:10:00 169.7270508 6495.13965 88.6335297 0.27961975

27-Aug-09 18:11:00 169.5645599 6484.90918 88.6948395 0.27961341

27-Aug-09 18:12:00 170.2315674 6478.12451 88.7561569 0.27960703

27-Aug-09 18:13:00 169.9719086 6485.58789 89.1285477 0.27960065

27-Aug-09 18:14:00 169.9351501 6498.28711 89.0162125 0.27959427

27-Aug-09 18:15:00 170.5043793 6486.56543 88.9038773 0.27958792

27-Aug-09 18:16:00 170.6784821 6520.10449 88.7915344 0.27958155

27-Aug-09 18:17:00 170.8525848 6517.58594 88.6791992 0.27957517

27-Aug-09 18:18:00 170.2444763 6503.67139 88.566864 0.27956879

27-Aug-09 18:19:00 169.6322479 6494.08252 88.4545288 0.27956241

27-Aug-09 18:20:00 169.1784515 6493.64258 88.7663727 0.27955607

27-Aug-09 18:21:00 169.9720459 6524.60254 88.2391281 0.27954969

27-Aug-09 18:22:00 170.3070068 6508.68848 88.0427475 0.27954331

27-Aug-09 18:23:00 170.4831085 6498.72656 87.9400864 0.27953693

27-Aug-09 18:24:00 170.1592102 6512.29395 87.8374252 0.27953058

27-Aug-09 18:25:00 170.3404083 6512.15967 87.6560516 0.27952421

27-Aug-09 18:26:00 170.0316925 6504.09277 87.444313 0.27951783

27-Aug-09 18:27:00 169.7476654 6471.6416 87.3673172 0.27951145

27-Aug-09 18:28:00 169.8645325 6463.85596 87.2903214 0.27950507

27-Aug-09 18:29:00 169.2492065 6489.90234 87.2133255 0.27949873

27-Aug-09 18:30:00 170.0969238 6495.59814 87.3993988 0.27949235

27-Aug-09 18:31:00 170.2050018 6485.69775 87.7073822 0.27948597

27-Aug-09 18:32:00 170.2743378 6459.30859 87.6939697 0.27947959

27-Aug-09 18:33:00 169.2555237 6489.79248 87.7224045 0.27947325

27-Aug-09 18:34:00 170.2921906 6517.19434 87.5677795 0.27946687

27-Aug-09 18:35:00 170.0969238 6491.40869 87.413147 0.27946049

Page 15 of 15
Plant Information Source: polk-1pisrv

Start Time: 09/01/2009 10:32

End Time: 09/01/2009 12:58

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 170.0567026 6587.21 79.881857 1.92634145

01-Sep-09 10:32:00 170.4930267 6569.86621 81.3327103 1.93360674

01-Sep-09 10:33:00 169.8574371 6579.58301 81.4093933 1.93355441

01-Sep-09 10:34:00 170.2223663 6589.71289 81.4860764 1.9335022

01-Sep-09 10:35:00 170.0543823 6622.64014 81.5571976 1.93344986

01-Sep-09 10:36:00 170.34758 6566.12549 81.3005447 1.93339765

01-Sep-09 10:37:00 170.6755981 6593.44336 81.0438919 1.93334532

01-Sep-09 10:38:00 170.9232483 6620.12256 80.7872314 1.9332931

01-Sep-09 10:39:00 170.7553711 6609.12207 80.5305786 1.93324077

01-Sep-09 10:40:00 170.6428986 6598.12158 80.2739258 1.93318856

01-Sep-09 10:41:00 170.5675812 6587.5249 80.0172653 1.93313622

01-Sep-09 10:42:00 170.2844849 6600.08301 80.2409821 1.93308401

01-Sep-09 10:43:00 169.9258423 6575.0542 80.1639862 1.93303168

01-Sep-09 10:44:00 170.3450317 6566.0708 80.0869904 1.93297946

01-Sep-09 10:45:00 169.5058746 6558.21484 80.0099945 1.93292713

01-Sep-09 10:46:00 169.7790375 6615.34619 80.1206207 1.93287492

01-Sep-09 10:47:00 169.9780273 6582.77002 80.2733612 1.93282259

01-Sep-09 10:48:00 169.6552277 6578.1377 80.1899643 1.93277037

01-Sep-09 10:49:00 169.7209167 6556.85791 80.0346985 1.93189442

01-Sep-09 10:50:00 169.7866058 6577.4165 79.8012543 1.92959595

01-Sep-09 10:51:00 169.830368 6557.27979 79.9509659 1.92729747

01-Sep-09 10:52:00 170.6894989 6603.13916 80.0934067 1.924999

01-Sep-09 10:53:00 170.883606 6606.84424 80.2054901 1.92360139

01-Sep-09 10:54:00 170.2178955 6591.64355 80.0502243 1.92365313

01-Sep-09 10:55:00 169.4880066 6589.34619 79.8810959 1.92370486

01-Sep-09 10:56:00 169.3265076 6574.07959 79.9346619 1.9237566

01-Sep-09 10:57:00 169.515625 6576.41455 79.8353958 1.92380822

01-Sep-09 10:58:00 170.1027222 6646.22998 79.7361298 1.92385995

01-Sep-09 10:59:00 170.5006714 6600.32178 79.7731323 1.92391169

01-Sep-09 11:00:00 170.4556427 6589.32129 79.9216309 1.92396343

01-Sep-09 11:01:00 171.0151825 6582.27295 79.6921692 1.92401516

01-Sep-09 11:02:00 170.3067474 6597.61768 79.3414307 1.92406678

01-Sep-09 11:03:00 170.1564636 6600.90771 79.2650528 1.92411852

01-Sep-09 11:04:00 169.1421204 6556.65039 79.1886826 1.92417026

01-Sep-09 11:05:00 169.6530609 6582.42773 79.1123123 1.92422199

Page 1 of 4
Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

01-Sep-09 11:06:00 170.0839691 6591.52148 79.305275 1.92427373

01-Sep-09 11:07:00 169.5222321 6582.86768 79.3783417 1.92432535

01-Sep-09 11:08:00 169.3961639 6617.79395 79.3783417 1.92437708

01-Sep-09 11:09:00 169.4734955 6594.14209 79.1340332 1.92442882

01-Sep-09 11:10:00 170.3675537 6600.61279 79.3404846 1.92448056

01-Sep-09 11:11:00 170.6805115 6603.25537 79.5469437 1.92453229

01-Sep-09 11:12:00 170.5108032 6591.2876 79.349411 1.92458391

01-Sep-09 11:13:00 170.4048309 6601.98389 79.2473068 1.92463565

01-Sep-09 11:14:00 170.9259338 6612.68066 79.1452026 1.92468739

01-Sep-09 11:15:00 170.9030914 6619.53516 79.0985794 1.92473912

01-Sep-09 11:16:00 170.2355957 6607.55371 79.2525787 1.92479086

01-Sep-09 11:17:00 170.3123169 6610.24268 79.7166214 1.92484248

01-Sep-09 11:18:00 170.4834137 6612.93164 79.867569 1.92489421

01-Sep-09 11:19:00 170.0961761 6610.05078 79.7002258 1.92494595

01-Sep-09 11:20:00 169.6735229 6579.32275 79.7753983 1.92499769

01-Sep-09 11:21:00 169.5558014 6557.45459 79.850563 1.9250493

01-Sep-09 11:22:00 169.4486084 6578.42627 79.9257278 1.92510104

01-Sep-09 11:23:00 169.7451172 6565.92725 79.7064285 1.92515278

01-Sep-09 11:24:00 169.6041718 6569.72266 80.3037796 1.92520452

01-Sep-09 11:25:00 169.5735626 6566.47705 80.3089981 1.92525625

01-Sep-09 11:26:00 169.9797058 6602.96191 79.7015839 1.92530787

01-Sep-09 11:27:00 170.0474854 6582.92285 79.6411209 1.92535961

01-Sep-09 11:28:00 169.6371613 6578.15576 79.5899277 1.92541134

01-Sep-09 11:29:00 169.1286926 6575.29639 79.5387421 1.92546308

01-Sep-09 11:30:00 169.9624329 6583.24658 79.4875488 1.92551482

01-Sep-09 11:31:00 169.871933 6595.37158 79.4363556 1.92556643

01-Sep-09 11:32:00 170.3100586 6618.7168 79.38517 1.92561817

01-Sep-09 11:33:00 170.5526733 6589.28223 79.7717896 1.92566991

01-Sep-09 11:34:00 169.3236237 6551.46143 80.225769 1.92572165

01-Sep-09 11:35:00 168.8619537 6583.83936 80.246376 1.92577338

01-Sep-09 11:36:00 170.1834106 6567.31104 80.169693 1.925825

01-Sep-09 11:37:00 171.0328827 6588.02881 80.0930099 1.92587674

01-Sep-09 11:38:00 170.6495667 6606.46387 80.0163269 1.92592847

01-Sep-09 11:39:00 170.0712585 6604.4834 79.6174774 1.92598021

01-Sep-09 11:40:00 170.2629242 6568.86084 79.5142517 1.92603195

01-Sep-09 11:41:00 170.1284485 6580.42969 79.411026 1.92608356

01-Sep-09 11:42:00 169.6867371 6582.73047 79.270546 1.9261353

01-Sep-09 11:43:00 170.3431244 6600.44385 79.1781464 1.92618704

01-Sep-09 11:44:00 169.7070313 6580.64307 79.3783417 1.92623878

01-Sep-09 11:45:00 169.5079041 6579.2373 79.3783417 1.92629051

Page 2 of 4
Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

01-Sep-09 11:46:00 169.8045502 6595.12695 79.6315765 1.92634213

01-Sep-09 11:47:00 169.75914 6571.36279 79.5289154 1.92639387

01-Sep-09 11:48:00 169.7769623 6604.96045 79.4262466 1.9264456

01-Sep-09 11:49:00 170.5748291 6602.28369 79.743309 1.92649734

01-Sep-09 11:50:00 170.4152069 6601.05029 79.8436737 1.92654896

01-Sep-09 11:51:00 169.3448181 6566.79492 79.9440308 1.92660069

01-Sep-09 11:52:00 169.858139 6575.7666 79.7380371 1.92662179

01-Sep-09 11:53:00 169.4442596 6557.0415 79.8378448 1.92658997

01-Sep-09 11:54:00 169.5765533 6566.59961 79.9376602 1.92655814

01-Sep-09 11:55:00 169.4186707 6569.04395 79.8711166 1.92652619

01-Sep-09 11:56:00 169.074585 6549.24316 79.8093033 1.92649436

01-Sep-09 11:57:00 169.9945984 6563.47021 79.9409866 1.92646253

01-Sep-09 11:58:00 170.7342377 6660.89697 79.7912674 1.9264307

01-Sep-09 11:59:00 170.7524109 6621.44336 79.7080078 1.92639887

01-Sep-09 12:00:00 170.6995544 6603.02295 79.757637 1.92636704

01-Sep-09 12:01:00 170.435379 6608.06396 79.8072739 1.9263351

01-Sep-09 12:02:00 170.405899 6606.84814 79.8569031 1.92630327

01-Sep-09 12:03:00 170.7313385 6605.63281 79.9065399 1.92627144

01-Sep-09 12:04:00 170.6330566 6605.49219 79.9561768 1.92623961

01-Sep-09 12:05:00 171.0271301 6610.36865 79.935997 1.92620778

01-Sep-09 12:06:00 170.286087 6580.04443 79.7463531 1.92617583

01-Sep-09 12:07:00 170.4086609 6606.33545 79.9451447 1.926144

01-Sep-09 12:08:00 170.5242462 6598.63477 79.4253082 1.92611217

01-Sep-09 12:09:00 170.2277832 6589.16895 79.4567566 1.92608035

01-Sep-09 12:10:00 169.5926666 6568.26758 79.9958801 1.92604852

01-Sep-09 12:11:00 170.0024414 6579.00879 80.3005829 1.92601669

01-Sep-09 12:12:00 169.3649597 6573.90381 80.1996231 1.92598474

01-Sep-09 12:13:00 170.1666412 6568.79834 80.0986633 1.92595291

01-Sep-09 12:14:00 169.9733276 6566.62354 79.9977036 1.92592108

01-Sep-09 12:15:00 170.261734 6587.67139 79.8967438 1.92588925

01-Sep-09 12:16:00 170.657959 6581.66797 79.795784 1.92585742

01-Sep-09 12:17:00 170.4340057 6593.56885 79.6948242 1.92582548

01-Sep-09 12:18:00 170.0708008 6641.01416 79.6657944 1.92579365

01-Sep-09 12:19:00 170.069046 6617.36328 79.4136963 1.92576182

01-Sep-09 12:20:00 170.4230652 6596.10791 79.6549301 1.92572999

01-Sep-09 12:21:00 169.9980164 6592.99121 79.4911499 1.92569816

01-Sep-09 12:22:00 170.184433 6591.82129 79.6213074 1.92566621

01-Sep-09 12:23:00 170.8148193 6603.63672 79.7514725 1.92563438

01-Sep-09 12:24:00 170.5036774 6599.625 79.8816299 1.92560256

01-Sep-09 12:25:00 169.6221924 6572.49072 80.011795 1.92557073

Page 3 of 4
Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

01-Sep-09 12:26:00 169.5121918 6548.5918 80.1419601 1.9255389

01-Sep-09 12:27:00 169.771225 6558.25146 80.2721176 1.92550707

01-Sep-09 12:28:00 169.5052948 6593.73389 80.2469559 1.92547512

01-Sep-09 12:29:00 169.5639496 6575.1499 80.1603851 1.92544329

01-Sep-09 12:30:00 170.1222992 6591.19141 80.0738144 1.92541146

01-Sep-09 12:31:00 170.1042633 6582.94141 79.9872437 1.92537963

01-Sep-09 12:32:00 169.6146393 6551.40674 79.9006729 1.92534781

01-Sep-09 12:33:00 169.1250153 6562.77344 79.8141022 1.92531586

01-Sep-09 12:34:00 169.594574 6575.2041 79.7275314 1.92528403

01-Sep-09 12:35:00 170.6145935 6594.59473 79.7780838 1.9252522

01-Sep-09 12:36:00 169.974823 6586.69336 79.9265823 1.92522037

01-Sep-09 12:37:00 170.0362701 6559.99268 79.9153748 1.92518854

01-Sep-09 12:38:00 170.4515991 6602.00244 79.7644196 1.92515671

01-Sep-09 12:39:00 170.2804871 6596.05078 79.9586029 1.92512476

01-Sep-09 12:40:00 170.0301361 6608.16846 79.8840485 1.92509294

01-Sep-09 12:41:00 169.5167694 6568.90918 79.8095016 1.92506111

01-Sep-09 12:42:00 169.1091766 6575.62939 79.7349472 1.92502928

01-Sep-09 12:43:00 170.4509888 6582.34912 79.8711166 1.92499745

01-Sep-09 12:44:00 170.5572662 6589.06885 79.8810959 1.9249655

01-Sep-09 12:45:00 170.753952 6591.47021 79.7160721 1.92493367

01-Sep-09 12:46:00 169.8368225 6564.05713 79.7831955 1.92490184

01-Sep-09 12:47:00 169.5136719 6564.48926 79.8503189 1.92487001

01-Sep-09 12:48:00 169.8128967 6580.44189 79.9174423 1.92483819

01-Sep-09 12:49:00 170.0007172 6581.95117 79.9845657 1.92480624

01-Sep-09 12:50:00 169.7071381 6567.38232 80.0516891 1.92477441

01-Sep-09 12:51:00 169.9154663 6575.76953 80.1188126 1.92474258

01-Sep-09 12:52:00 170.4890594 6584.15625 80.185936 1.92471075

01-Sep-09 12:53:00 170.5772095 6589.35791 80.2530594 1.92467892

01-Sep-09 12:54:00 169.4154663 6569.92383 80.2987671 1.92464709

01-Sep-09 12:55:00 170.4129181 6584.48096 80.2373734 1.92461514

01-Sep-09 12:56:00 169.9683075 6578.24756 80.175972 1.92458332

01-Sep-09 12:57:00 169.621994 6572.01416 80.1145782 1.92455149

01-Sep-09 12:58:00 169.2756805 6565.78076 80.0531845 1.92451966

Page 4 of 4
APPENDIX C 

FUEL ANALYSIS 
UNIT 1 HRSG ACID MIST STACK TEST

08/27/2009

Calibration Standard Check

% CO2 % Ar % N2 % CO % H2 % H2S/COS

True Value 15.10 1.00 2.99 43.90 36.90 N.A.

Std. 1 15.09 1.02 3.00 43.94 36.95 N.A.

Std. 2 15.08 1.02 2.99 43.70 37.21 N.A.

Avg. 15.09 1.02 3.00 43.82 37.08 N.A.

Clean Syngas 

Time Sampled % CO2 % Ar2 % N2 % CO % H2 % H2S/COS

820 15.04 0.88 2.30 46.29 35.49 N.A.

820 15.11 0.86 2.89 46.58 35.18 N.A.

930 15.15 0.84 2.53 46.61 34.87 N.A.

930 15.24 0.86 2.25 46.66 34.99 N.A.

1230 15.46 0.86 2.18 46.47 35.03 N.A.

1400 15.40 0.87 2.29 46.69 34.75 N.A.

1400 15.43 0.87 2.28 46.78 34.64 N.A.

Avg. 15.26 0.86 2.39 46.58 34.99 0

Mole Wt. 21.48

HHV BTU/SCF 263.71

HHV BTU/Lb 4627
Natural Gas and Heating Value Calculations

Customer: Tampa Electric Company

Facility: Polk Power Station

Source: Unit 1

CALCULATION OF DENSITY AND HEATING VALUE @ 68°F and 29.92 in Hg

% volume Component Gross * Volume

% Molecular Density * x Gross Weight Heating Value Fract.

Component Volume Wt. (lb/ft3

) Density weight % Btu/lb Fract. Btu (Btu/SCF) Btu

Hydrogen 34.9900 2.016 0.0053 0.00185 3.2608 61100 1992.34 325.0 113.7175

Oxygen 0.0000 32.000 0.0846 0.00000 0.0000 0 0.00 0.0 0

Nitrogen 2.3900 28.014 0.0744 0.00178 3.1266 0 0.00 0.0 0

CO2 15.2600 44.010 0.1170 0.01785 31.3937 0 0.00 0.0 0

CO 46.5800 28.010 0.0740 0.03447 60.6085 4347 2634.65 322.0 149.9876

Argon 0.8600 39.948 0.1065 0.00092 0.1232 0 0.00 0.0 0

Total: 100.08 Average Density 0.05687 98.5127 Gross Heating Value

Specific Gravity 0.74342 Btu/lb 4627 Btu/SCF 263.71

Btu/lb 4325 Btu/SCF 246

*

 Density (lb/ft3) and Gross Heating Value (Btu/scf) data from Perry's Chemical Engineering Hanbook.

Net Heating Value (Lower Heating Value), Btu/lb, calculated as Gross Heating Value (Higher Heating Value) - 10.30 (%H2 x 8.94)

CALCULATION OF F FACTORS 

Weight Percents

Component Mol. Wt. C Factor H Factor % volume Fract. Wt. Carbon Hydrogen Nitrogen Oxygen

Hydrogen 2.016 0 1 34.990 70.5398 3.283753

Oxygen 32.000 0 0 0.000 0.0000 0

Nitrogen 28.014 0 0 2.390 66.9535 3.116800695

CO2 44.010 0.272273 0 15.260 671.5926 8.51229146 22.72879

CO 28.010 0.42587 0 46.580 1304.7058 25.8657841 34.905173

Argon 39.948 0 0 0.860 34.3553

Totals 100.08000 2148.1470 34.3780755 3.28 3.116800695 57.633963

CALCULATED VALUES

O2 F Factor (dry), Fd 8316 DSCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air

O2 F Factor (wet), Fw 9685 SCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air

Moisture F Factor 1370 SCF of Water/MM Btu of Fuel Burned @ 0% excess air

Combust. Moisture 14.14 volume % water in flue gas @ 0% excess air

CO2 F Factor, Fc 2385 DSCF of CO2/MM Btu of Fuel Burned @ 0% excess air

Carbon Dioxide 28.68 volume % CO2 in flue gas @ 0% O2

Predicted Fo Factor 0.73 EPA Method 3a Fo value

Net Heating Values
APPENDIX D 

CEMS DATA 
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

08/27/2009 7:47 43.14 18.9 8.8 10.3 759.6

08/27/2009 7:48 43.67 19.3 8.8 10.4 771

08/27/2009 7:49 43.94 19.1 8.8 10.4 763.9

08/27/2009 7:50 44.33 18.8 8.8 10.4 753.3

08/27/2009 7:51 44.38 18.8 8.8 10.4 755.3

08/27/2009 7:52 44.26 18.9 8.8 10.4 758.8

08/27/2009 7:53 43.69 18.9 8.8 10.4 761.1

08/27/2009 7:54 44.18 19.1 8.8 10.4 751.9

08/27/2009 7:55 44.32 19.1 8.8 10.4 753.2

08/27/2009 7:56 44.7 18.9 8.8 10.4 760

08/27/2009 7:57 44.98 19.1 8.8 10.4 768.2

08/27/2009 7:58 45.28 19.2 8.8 10.4 767.6

08/27/2009 7:59 44.96 19.1 8.8 10.4 784

08/27/2009 8:00 44.78 19.3 8.8 10.4 764.8

08/27/2009 8:01 43.97 19.6 8.8 10.4 783.8

08/27/2009 8:02 44.23 19.8 8.8 10.4 768.2

08/27/2009 8:03 44.47 19.4 8.8 10.4 762.8

08/27/2009 8:04 44.64 19.3 8.8 10.4 756.2

08/27/2009 8:05 44.24 19.5 8.8 10.4 742.8

08/27/2009 8:06 43.4 19.9 8.8 10.4 753.2

08/27/2009 8:07 43.94 19.8 8.8 10.4 760

08/27/2009 8:08 44.07 20.3 8.8 10.4 765.6

08/27/2009 8:09 44.31 19.7 8.8 10.4 770.6

08/27/2009 8:10 44.03 19.7 8.8 10.4 773.1

08/27/2009 8:11 43.93 19.6 8.8 10.4 762.9

08/27/2009 8:12 44.66 19.6 8.8 10.4 745.9

08/27/2009 8:13 44.09 19.9 8.8 10.4 758

08/27/2009 8:14 44.41 19.7 8.8 10.4 763.3

08/27/2009 8:15 43.93 19.2 8.8 10.4 755.6

08/27/2009 8:16 43.38 19.4 8.8 10.4 757.7

08/27/2009 8:17 43.64 19.6 8.8 10.4 764.8

08/27/2009 8:18 43.86 19.7 8.8 10.4 770.4

08/27/2009 8:19 44.08 19.3 8.8 10.4 764.2

08/27/2009 8:20 44.72 19.5 8.8 10.4 766.7

08/27/2009 8:21 44.99 19.4 8.8 10.4 756.8

08/27/2009 8:22 45 19.3 8.8 10.4 775.3

08/27/2009 8:23 44.89 19.3 8.8 10.4 766.5

08/27/2009 8:24 45.05 19.2 8.8 10.4 764.1

08/27/2009 8:25 44.84 19.3 8.8 10.4 751.7

08/27/2009 8:26 44.96 19.6 8.8 10.4 764.8

08/27/2009 8:27 44.86 19.6 8.8 10.4 771.7

Run 1

Page 1 of 16
CEMS Data

08/27/2009 8:28 44.64 19.5 8.8 10.4 762.8

08/27/2009 8:29 44.72 19.5 8.8 10.4 766.4

08/27/2009 8:30 44.54 19.8 8.8 10.4 765.5

08/27/2009 8:31 44.4 19.6 8.8 10.4 763

08/27/2009 8:32 44.37 19.2 8.8 10.4 768.5

08/27/2009 8:33 44.61 19.5 8.8 10.4 787.2

08/27/2009 8:34 45.15 19.4 8.8 10.4 780.4

08/27/2009 8:35 45.56 19.4 8.9 10.4 761.1

08/27/2009 8:36 44.66 19.6 8.9 10.4 745.7

08/27/2009 8:37 44.07 19.7 8.9 10.4 768.9

08/27/2009 8:38 44.09 19.6 8.9 10.4 777.8

08/27/2009 8:39 44.43 19.7 8.9 10.4 778

08/27/2009 8:40 44.27 19.5 8.9 10.4 763.9

08/27/2009 8:41 44.78 19.6 8.9 10.4 775.8

08/27/2009 8:42 44.97 19.9 8.9 10.4 776.8

08/27/2009 8:43 45.09 19.6 8.8 10.4 785

08/27/2009 8:44 45.47 19.5 8.8 10.4 787.6

08/27/2009 8:45 44.74 19.1 8.8 10.4 781

08/27/2009 8:46 43.75 19.4 8.8 10.4 770.3

08/27/2009 8:47 43.79 19.7 8.8 10.5 764.5

08/27/2009 8:48 43.74 20.2 8.8 10.5 756.7

08/27/2009 8:49 44.11 20.2 8.8 10.5 773.3

08/27/2009 8:50 44.25 20 8.8 10.4 766.8

08/27/2009 8:51 44.34 19.6 8.8 10.5 788.1

08/27/2009 8:52 44.58 19.6 8.8 10.5 759.6

08/27/2009 8:53 44.48 19.8 8.8 10.5 777.8

08/27/2009 8:54 44.11 19.8 8.8 10.4 770

08/27/2009 8:55 44.48 20.1 8.9 10.5 780.1

08/27/2009 8:56 44.08 20.2 8.8 10.4 782.7

08/27/2009 8:57 44.46 20 8.8 10.4 782.8

44.39 19.51 8.81 10.41 766.73

766725.4

724870.752

Page 2 of 16
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

08/27/2009 9:30 44.16 20.9 8.9 10.5 771.4

08/27/2009 9:31 44 20.7 8.9 10.5 770.9

08/27/2009 9:32 43.64 20.3 8.9 10.5 771.2

08/27/2009 9:33 43.76 20.5 8.8 10.5 772.4

08/27/2009 9:34 44.17 20.1 8.8 10.4 780.8

08/27/2009 9:35 43.94 19.6 8.8 10.4 779

08/27/2009 9:36 43.15 19.9 8.8 10.5 783.7

08/27/2009 9:37 43.34 20 8.8 10.5 790.8

08/27/2009 9:38 43.33 20.4 8.8 10.5 784.8

08/27/2009 9:39 43.82 20.2 8.8 10.5 783.5

08/27/2009 9:40 43.91 20.3 8.9 10.5 773.6

08/27/2009 9:41 44.06 20.1 8.8 10.5 779.5

08/27/2009 9:42 44.1 20.4 8.9 10.4 777.6

08/27/2009 9:43 44.52 20.2 8.9 10.4 759.4

08/27/2009 9:44 44.35 20.4 8.9 10.5 762.5

08/27/2009 9:45 44.04 20.3 8.8 10.5 767.8

08/27/2009 9:46 44.06 20.3 8.9 10.5 766.8

08/27/2009 9:47 44.17 20.5 8.9 10.5 762.4

08/27/2009 9:48 43.8 20.2 8.8 10.5 773.5

08/27/2009 9:49 43.41 20 8.8 10.5 781

08/27/2009 9:50 43.54 20.6 8.9 10.5 781.1

08/27/2009 9:51 43.62 20.4 8.9 10.5 784.5

08/27/2009 9:52 44.04 20.3 8.9 10.5 753.6

08/27/2009 9:53 43.71 20.3 8.9 10.5 771.4

08/27/2009 9:54 43.51 20.3 8.9 10.5 764.8

08/27/2009 9:55 42.9 20 8.9 10.5 779.4

08/27/2009 9:56 42.93 20.1 8.9 10.5 773.4

08/27/2009 9:57 43.4 20.3 8.9 10.5 774.2

08/27/2009 9:58 43.16 20.5 8.9 10.5 761

08/27/2009 9:59 43.48 20.5 8.9 10.5 750

08/27/2009 10:00 43.61 20.5 8.9 10.5 761.8

08/27/2009 10:01 43.52 20.5 8.9 10.5 769.4

08/27/2009 10:02 43.78 20.8 8.9 10.5 775.9

08/27/2009 10:03 44.33 20.8 8.8 10.5 775.5

08/27/2009 10:04 44.83 20.6 8.8 10.5 783.7

08/27/2009 10:05 44.98 20 8.8 10.5 782.8

08/27/2009 10:06 43.96 20.2 8.8 10.6 771.6

08/27/2009 10:07 43.19 20.8 8.9 10.5 765.2

08/27/2009 10:08 43.51 21.1 8.9 10.5 780

08/27/2009 10:09 43.74 21.2 8.9 10.5 760.4

08/27/2009 10:10 43.71 21.1 8.9 10.5 767.1

Run 2

Page 3 of 16
CEMS Data

08/27/2009 10:11 44.25 21.4 8.9 10.5 790.5

08/27/2009 10:12 43.42 20.9 8.9 10.5 782.2

08/27/2009 10:13 43.96 20.7 8.8 10.6 767.1

08/27/2009 10:14 44.19 21.1 8.8 10.5 762.7

08/27/2009 10:15 44.6 20.9 8.8 10.5 759.6

08/27/2009 10:16 44.59 20.7 8.9 10.5 773.5

08/27/2009 10:17 44.51 21.2 8.9 10.5 761.5

08/27/2009 10:18 44.29 21.1 8.8 10.5 777.4

08/27/2009 10:19 44.3 21.2 8.9 10.5 771.8

08/27/2009 10:20 44.43 20.7 8.9 10.5 770.1

08/27/2009 10:21 44.49 20.9 8.8 10.5 766.5

08/27/2009 10:22 44.89 21 8.8 10.6 763.5

08/27/2009 10:23 44.64 21.1 8.8 10.5 776.3

08/27/2009 10:24 44.28 20.9 8.9 10.5 755.9

08/27/2009 10:25 44.06 20.3 8.9 10.4 756.1

08/27/2009 10:26 43.62 20.2 8.9 10.5 767

08/27/2009 10:27 43.8 20.6 8.9 10.5 762.2

08/27/2009 10:28 44.41 20.5 8.9 10.4 766.4

08/27/2009 10:29 44.43 20.6 8.9 10.5 760.1

08/27/2009 10:30 44.9 20.6 8.9 10.5 765.8

08/27/2009 10:31 45.23 20.5 8.8 10.5 771.5

08/27/2009 10:32 44.63 20.4 8.9 10.5 775.8

08/27/2009 10:33 44.26 20.1 8.9 10.4 774.2

08/27/2009 10:34 44.39 20 8.9 10.5 775.2

08/27/2009 10:35 44.54 20.4 8.9 10.5 781.7

08/27/2009 10:36 44.56 20.3 8.9 10.5 766.7

08/27/2009 10:37 44.45 20.5 8.9 10.5 767.5

08/27/2009 10:38 44.16 20 8.8 10.5 765.3

08/27/2009 10:39 44.94 19.8 8.8 10.5 773.9

44.03 20.50 8.86 10.49 771.25

771248.6

719169.55

Page 4 of 16
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

08/27/2009 10:58 46.07 20.2 8.9 10.5 767.5

08/27/2009 10:59 46.68 20 8.8 10.5 786.1

08/27/2009 11:00 46.24 19.7 8.9 10.5 759.1

08/27/2009 11:01 46.9 19.7 8.8 10.5 771.3

08/27/2009 11:02 46.43 20.2 8.9 10.5 761.4

08/27/2009 11:03 45.92 20.5 8.9 10.5 773.5

08/27/2009 11:04 46.25 19.9 8.9 10.5 779.9

08/27/2009 11:05 45.78 19.8 8.9 10.5 781.2

08/27/2009 11:06 45.53 19.9 8.9 10.5 780.4

08/27/2009 11:07 46 19.8 8.8 10.5 766

08/27/2009 11:08 46.14 19.9 8.9 10.5 783.4

08/27/2009 11:09 46.35 19.8 8.8 10.5 790.9

08/27/2009 11:10 46.57 19.8 8.8 10.5 790.6

08/27/2009 11:11 46.37 19.9 8.9 10.4 778.1

08/27/2009 11:12 46.2 19.9 8.9 10.5 761.5

08/27/2009 11:13 46.3 20.1 8.9 10.5 753.2

08/27/2009 11:14 45.91 19.9 8.9 10.5 764.3

08/27/2009 11:15 45.5 19.2 8.9 10.4 793.9

08/27/2009 11:16 45.27 19.6 8.9 10.5 791.9

08/27/2009 11:17 45.19 20 8.9 10.5 781.7

08/27/2009 11:18 45.8 19.9 8.9 10.5 766

08/27/2009 11:19 46.53 19.4 8.9 10.5 767.4

08/27/2009 11:20 46.88 19.5 8.9 10.5 763.8

08/27/2009 11:21 46.34 19.6 8.9 10.5 766.7

08/27/2009 11:22 46.45 19.9 8.9 10.5 767.9

08/27/2009 11:23 46.67 20 8.9 10.5 784.4

08/27/2009 11:24 47.01 19.6 8.9 10.4 763.8

08/27/2009 11:25 46.77 19.4 8.9 10.4 766.8

08/27/2009 11:26 45.8 19.4 8.9 10.5 758.1

08/27/2009 11:27 46.1 19.6 8.9 10.5 751.3

08/27/2009 11:28 46.8 19.8 8.9 10.5 758.2

08/27/2009 11:29 46.92 19.9 8.9 10.5 763.5

08/27/2009 11:30 47.04 20 8.9 10.5 761.5

08/27/2009 11:31 46.38 19.8 8.9 10.5 756.2

08/27/2009 11:32 46.51 19.6 8.9 10.5 771.1

08/27/2009 11:33 46.44 19.8 8.9 10.5 772.7

08/27/2009 11:34 45.69 19.5 8.9 10.5 774.1

08/27/2009 11:35 46.28 19.7 8.9 10.5 771.2

08/27/2009 11:36 46.45 19.7 8.8 10.5 769.8

08/27/2009 11:37 46.5 19.6 8.9 10.5 760.4

08/27/2009 11:38 47.11 19.8 8.9 10.5 769

Run 3

Page 5 of 16
CEMS Data

08/27/2009 11:39 47.06 19.6 8.8 10.5 777

08/27/2009 11:40 46.86 19.9 8.9 10.5 769.5

08/27/2009 11:41 46.56 19.9 8.8 10.5 783.5

08/27/2009 11:42 45.98 20 8.8 10.5 767.7

08/27/2009 11:43 45.42 20 8.8 10.5 801

08/27/2009 11:44 45.62 20.2 8.8 10.4 778

08/27/2009 11:45 45.41 19.6 8.9 10.4 766.8

08/27/2009 11:46 45.14 19.3 8.8 10.4 774

08/27/2009 11:47 45.71 19.3 8.8 10.4 763.6

08/27/2009 11:48 46.19 19.2 8.8 10.5 764.1

08/27/2009 11:49 46.39 19.4 8.8 10.5 761

08/27/2009 11:50 46.71 19.5 8.9 10.4 777.3

08/27/2009 11:51 47.01 19.3 8.9 10.4 777.1

08/27/2009 11:52 47.76 19.3 8.9 10.4 762.3

08/27/2009 11:53 47.94 19.2 8.9 10.4 777.1

08/27/2009 11:54 47.78 19.4 8.9 10.4 768.1

08/27/2009 11:55 47.73 19.6 8.9 10.4 765.2

08/27/2009 11:56 46.97 19.3 8.9 10.4 780

08/27/2009 11:57 46.46 19.7 8.9 10.4 774.9

08/27/2009 11:58 45.13 20 8.9 10.4 770.5

08/27/2009 11:59 45.08 19.7 8.9 10.4 765.4

08/27/2009 12:00 44.87 19.5 8.9 10.5 763.2

08/27/2009 12:01 44.28 19.6 8.9 10.4 768.8

08/27/2009 12:02 43.97 20 8.9 10.4 784.1

08/27/2009 12:03 43.48 20.1 8.9 10.4 773.8

08/27/2009 12:04 43.82 20 8.9 10.4 779.6

08/27/2009 12:05 43.79 19.8 8.9 10.4 780.9

08/27/2009 12:06 43.98 19.6 8.9 10.4 769.8

46.10 19.73 8.88 10.47 771.65

771653.6

720832.834

Page 6 of 16
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

08/27/2009 12:25 42.74 19.8 8.8 10.5 772.9

08/27/2009 12:26 40.31 14.4 4.8 10.5 753.5

08/27/2009 12:27 6.94 0.2 0 10.5 773.6

08/27/2009 12:28 18.89 11.4 7.6 10.5 769.1

08/27/2009 12:29 40.48 18.7 8.8 10.5 765.8

08/27/2009 12:30 42.81 19.5 8.8 10.5 768.8

08/27/2009 12:31 43.14 19.5 8.8 10.5 758.6

08/27/2009 12:32 42.53 19.7 8.8 10.5 779.1

08/27/2009 12:33 42.5 19.7 8.8 10.5 773.9

08/27/2009 12:34 43.32 19.7 8.8 10.5 774.1

08/27/2009 12:35 43.51 19.3 8.8 10.5 781.6

08/27/2009 12:36 43.33 19.6 8.8 10.5 766.3

08/27/2009 12:37 43.02 19.8 8.8 10.5 768

08/27/2009 12:38 43.06 19.9 8.8 10.5 776.2

08/27/2009 12:39 43.34 19.7 8.8 10.5 756.6

08/27/2009 12:40 43.56 19.8 8.8 10.5 741.5

08/27/2009 12:41 43.29 19.7 8.8 10.5 762.6

08/27/2009 12:42 43.19 19.9 8.8 10.5 771

08/27/2009 12:43 42.84 19.7 8.8 10.5 773.8

08/27/2009 12:44 43.57 19.7 8.8 10.4 774.4

08/27/2009 12:45 43.32 19.1 8.8 10.4 772.3

08/27/2009 12:46 43.2 19.3 8.8 10.5 771.1

08/27/2009 12:47 43.28 19.4 8.8 10.5 776

08/27/2009 12:48 43.26 19.5 8.8 10.5 774.7

08/27/2009 12:49 43.31 19.7 8.8 10.5 763.7

08/27/2009 12:50 43.02 19.7 8.8 10.4 777.6

08/27/2009 12:51 43.26 19.5 8.8 10.4 811.3

08/27/2009 12:52 43.29 19.7 8.8 10.5 770.8

08/27/2009 12:53 43.2 19.4 8.8 10.4 770.6

08/27/2009 12:54 43.75 19.2 8.8 10.5 760.2

08/27/2009 12:55 43.7 19.3 8.8 10.5 781.1

08/27/2009 12:56 43.34 19.3 8.8 10.5 773.5

08/27/2009 12:57 43.09 19.6 8.8 10.5 775.4

08/27/2009 12:58 42.83 19.7 8.8 10.4 787.9

08/27/2009 12:59 42.93 19.5 8.8 10.5 799.9

08/27/2009 13:00 42.83 19.5 8.8 10.5 764.2

08/27/2009 13:01 42.95 19.7 8.8 10.5 783.1

08/27/2009 13:02 43.37 19.4 8.8 10.5 785

08/27/2009 13:03 43.03 19.5 8.8 10.4 780.3

08/27/2009 13:04 42.76 19.3 8.8 10.4 760.5

08/27/2009 13:05 43.5 19.3 8.9 10.4 767

Run 4

Page 7 of 16
CEMS Data

08/27/2009 13:06 42.56 19.1 8.8 10.4 775.3

08/27/2009 13:07 43.05 19.4 8.8 10.4 763.4

08/27/2009 13:08 42.54 19.4 8.8 10.4 748

08/27/2009 13:09 42.66 19.1 8.8 10.4 754.7

08/27/2009 13:10 43.12 19.2 8.8 10.4 774.6

08/27/2009 13:11 43.15 19.5 8.8 10.4 769.7

08/27/2009 13:12 43.08 19.9 8.9 10.5 771.4

08/27/2009 13:13 43.08 19.5 8.8 10.4 775.6

08/27/2009 13:14 43.8 19.4 8.8 10.4 776.5

08/27/2009 13:15 44.01 19.6 8.8 10.5 783.3

08/27/2009 13:16 44.07 19.8 8.8 10.5 780.1

08/27/2009 13:17 44.19 19.7 8.8 10.5 760.2

08/27/2009 13:18 43.78 20 8.8 10.5 762.5

08/27/2009 13:19 43.24 20 8.8 10.5 780.8

08/27/2009 13:20 42.8 19.9 8.8 10.5 785.1

08/27/2009 13:21 43.17 19.8 8.8 10.5 775.7

08/27/2009 13:22 43.33 19.8 8.8 10.5 767.5

08/27/2009 13:23 42.95 19.9 8.8 10.5 765.7

08/27/2009 13:24 43.52 20.2 8.8 10.5 785.4

08/27/2009 13:25 43.52 20 8.9 10.4 765.6

08/27/2009 13:26 42.34 20.1 8.9 10.5 766.3

08/27/2009 13:27 42.12 20 8.8 10.5 770.5

08/27/2009 13:28 43 19.9 8.8 10.5 781.3

08/27/2009 13:29 43.13 20 8.8 10.5 792.8

08/27/2009 13:30 43.37 20.2 8.8 10.5 791.5

08/27/2009 13:31 43.37 20.2 8.8 10.5 780.2

08/27/2009 13:32 43.69 20 8.8 10.5 775.4

08/27/2009 13:33 43.36 19.9 8.8 10.4 758.2

42.23 19.16 8.60 10.47 772.53

772534.8

679950.986

Page 8 of 16
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

08/27/2009 15:24 43.87 20.3 8.8 10.5 764.8

08/27/2009 15:25 43.26 19.6 8.8 10.5 751.9

08/27/2009 15:26 42.71 19.8 8.8 10.5 753.1

08/27/2009 15:27 42.31 20.5 8.8 10.5 762.2

08/27/2009 15:28 42.78 20.6 8.8 10.5 762.5

08/27/2009 15:29 43.28 20.4 8.8 10.5 777.3

08/27/2009 15:30 43.46 20.2 8.8 10.5 763.6

08/27/2009 15:31 43.15 20.3 8.8 10.5 767

08/27/2009 15:32 42.96 20.4 8.8 10.5 768.1

08/27/2009 15:33 42.95 20.6 8.8 10.5 778.1

08/27/2009 15:34 43.06 20.9 8.8 10.5 779

08/27/2009 15:35 43.09 20.3 8.8 10.5 767.6

08/27/2009 15:36 43.13 20.4 8.8 10.5 785.4

08/27/2009 15:37 42.97 20.4 8.8 10.5 784.4

08/27/2009 15:38 42.96 20.5 8.8 10.5 771.6

08/27/2009 15:39 42.97 20.7 8.8 10.5 755

08/27/2009 15:40 42.61 20.7 8.8 10.5 770.8

08/27/2009 15:41 42.28 20.7 8.8 10.5 761.3

08/27/2009 15:42 42.6 20.5 8.8 10.5 767.2

08/27/2009 15:43 42.42 20.2 8.8 10.5 771.2

08/27/2009 15:44 43.15 19.8 8.8 10.5 778.8

08/27/2009 15:45 43.63 19.8 8.8 10.4 763.9

08/27/2009 15:46 43.47 19.7 8.8 10.5 766.7

08/27/2009 15:47 43.2 20.2 8.8 10.5 759.6

08/27/2009 15:48 43.4 20.6 8.8 10.5 775

08/27/2009 15:49 43.27 20.9 8.8 10.5 779.4

08/27/2009 15:50 43.69 20.5 8.8 10.5 781.3

08/27/2009 15:51 43.14 20.2 8.8 10.5 776.6

08/27/2009 15:52 43.26 20.3 8.8 10.5 751.9

08/27/2009 15:53 43.47 20.8 8.8 10.5 768.8

08/27/2009 15:54 43.28 21.1 8.8 10.5 783

08/27/2009 15:55 43.3 20.7 8.8 10.5 780.1

08/27/2009 15:56 42.84 20.8 8.8 10.5 775.2

08/27/2009 15:57 42.89 21.2 8.8 10.6 773.3

08/27/2009 15:58 42.5 21.1 8.8 10.5 776.5

08/27/2009 15:59 42.01 20.9 8.8 10.5 777.2

08/27/2009 16:00 41.71 21 8.8 10.6 778.2

08/27/2009 16:01 41.34 21.4 8.8 10.6 783.1

08/27/2009 16:02 40.94 21.4 8.8 10.6 767.6

08/27/2009 16:03 40.78 21.5 8.8 10.6 777.7

08/27/2009 16:04 41.21 21.3 8.8 10.5 774.5

Run 5

Page 9 of 16
CEMS Data

08/27/2009 16:05 41.31 21.2 8.8 10.5 767.8

08/27/2009 16:06 41.06 21 8.8 10.6 777.7

08/27/2009 16:07 41.05 21.2 8.8 10.6 769.5

08/27/2009 16:08 41.79 21.4 8.8 10.6 774.2

08/27/2009 16:09 42.04 21.9 8.9 10.6 778.1

08/27/2009 16:10 41.48 21.7 8.8 10.6 774.4

08/27/2009 16:11 41.9 21.3 8.8 10.6 759.5

08/27/2009 16:12 41.46 21.4 8.8 10.6 773.3

08/27/2009 16:13 41.38 21.5 8.8 10.6 775.6

08/27/2009 16:14 41.81 21.6 8.8 10.6 771.2

08/27/2009 16:15 42.21 21 8.8 10.5 766.7

08/27/2009 16:16 41.61 20.5 8.8 10.6 785.8

08/27/2009 16:17 41.9 21.1 8.8 10.6 762.4

08/27/2009 16:18 41.66 21.1 8.8 10.6 786.9

08/27/2009 16:19 41.92 21 8.8 10.6 758.7

08/27/2009 16:20 41.8 21 8.8 10.6 776.7

08/27/2009 16:21 41.91 21 8.8 10.5 795.2

08/27/2009 16:22 42.4 20.9 8.8 10.6 781.8

08/27/2009 16:23 42.9 20.7 8.8 10.5 776.3

08/27/2009 16:24 42.83 20.9 8.8 10.5 772.2

08/27/2009 16:25 42.25 20.9 8.8 10.5 769.7

08/27/2009 16:26 42.08 21.1 8.8 10.5 770.1

08/27/2009 16:27 42.73 20.8 8.8 10.5 786.5

08/27/2009 16:28 42.76 20.7 8.8 10.5 779.5

08/27/2009 16:29 42.59 20.5 8.8 10.5 769.6

08/27/2009 16:30 42.64 20.8 8.8 10.5 781.6

08/27/2009 16:31 42.11 20.8 8.8 10.5 771.8

08/27/2009 16:32 42.07 20.9 8.8 10.5 785.5

42.477536 20.77 8.801 10.53 772.591304

772591.3

690705.595

Page 10 of 16
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

08/27/2009 16:45 43.02 20.3 8.8 10.5 763.4

08/27/2009 16:46 42.09 20.4 8.8 10.5 792.4

08/27/2009 16:47 41.35 20.8 8.8 10.6 775.1

08/27/2009 16:48 41.52 21.3 8.8 10.5 763.5

08/27/2009 16:49 41.61 21.1 8.8 10.5 756.3

08/27/2009 16:50 42.01 21.1 8.8 10.6 771.6

08/27/2009 16:51 41.85 20.9 8.8 10.6 783

08/27/2009 16:52 41.58 21.1 8.8 10.6 798.6

08/27/2009 16:53 41.33 20.9 8.8 10.6 784

08/27/2009 16:54 41.44 21.1 8.8 10.6 770.7

08/27/2009 16:55 41.13 21.3 8.8 10.6 778.7

08/27/2009 16:56 41.28 21.2 8.8 10.6 780.7

08/27/2009 16:57 40.47 21.2 8.8 10.6 765.9

08/27/2009 16:58 40.77 21.5 8.8 10.6 766.1

08/27/2009 16:59 40.89 21.4 8.8 10.6 766

08/27/2009 17:00 41.21 21.3 8.8 10.6 776.9

08/27/2009 17:01 41.54 21 8.8 10.5 761.4

08/27/2009 17:02 41.51 20.8 8.8 10.5 766.8

08/27/2009 17:03 41.34 20.7 8.8 10.5 779.8

08/27/2009 17:04 42.01 20.8 8.8 10.5 760.8

08/27/2009 17:05 42.07 20.3 8.8 10.5 738.9

08/27/2009 17:06 41.6 20.4 8.8 10.5 770.6

08/27/2009 17:07 41.34 20.7 8.8 10.5 780.4

08/27/2009 17:08 41.19 20.7 8.8 10.5 762.9

08/27/2009 17:09 41.74 20.9 8.8 10.5 773.6

08/27/2009 17:10 42.15 21.2 8.8 10.5 778.4

08/27/2009 17:11 41.86 21.4 8.8 10.5 777.8

08/27/2009 17:12 41.75 20.9 8.8 10.6 763.7

08/27/2009 17:13 42.62 21.1 8.8 10.6 789

08/27/2009 17:14 42.53 21.2 8.8 10.5 795.8

08/27/2009 17:15 41.76 21.1 8.8 10.5 773.1

08/27/2009 17:16 41.64 21.4 8.8 10.5 782.5

08/27/2009 17:17 41.37 21.5 8.8 10.5 781.5

08/27/2009 17:18 41.6 21.5 8.8 10.5 772.7

08/27/2009 17:19 41.57 21.3 8.8 10.5 761.6

08/27/2009 17:20 41.52 21.3 8.8 10.5 764.5

08/27/2009 17:21 41.74 21.4 8.8 10.5 774.1

08/27/2009 17:22 41.65 21.5 8.8 10.5 761.5

08/27/2009 17:23 42.03 21.5 8.8 10.5 772.8

08/27/2009 17:24 42.14 21.2 8.8 10.5 783.6

08/27/2009 17:25 42.05 21.1 8.8 10.5 782.4

Run 6

Page 11 of 16
CEMS Data

08/27/2009 17:26 41.7 21.2 8.8 10.5 777

08/27/2009 17:27 41.3 21.4 8.8 10.5 777.1

08/27/2009 17:28 41.06 21.1 8.8 10.5 777.8

08/27/2009 17:29 40.9 21.2 8.8 10.6 788.3

08/27/2009 17:30 41.03 21.7 8.8 10.5 778.8

08/27/2009 17:31 40.99 21.7 8.8 10.5 777.3

08/27/2009 17:32 41.13 21.4 8.8 10.5 768.4

08/27/2009 17:33 41.58 21.6 8.8 10.5 761.2

08/27/2009 17:34 41.08 21.7 8.8 10.5 767

08/27/2009 17:35 41.06 21.1 8.8 10.5 766

41.56 21.14 8.80 10.53 773.37

773372.549

716724.554

Average for test day 43.47 20.13 8.79 10.48 771.35

771354.364

708709.045

Page 12 of 16
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

09/01/2009 9:32 45.5 17.5 8.8 10.3 779.5

09/01/2009 9:33 45.58 17.6 8.8 10.4 768

09/01/2009 9:34 45.5 17.6 8.8 10.4 775.6

09/01/2009 9:35 44.95 17.6 8.8 10.4 786.4

09/01/2009 9:36 45.08 18 8.8 10.4 768.4

09/01/2009 9:37 44.65 17.9 8.8 10.4 794.8

09/01/2009 9:38 44.28 17.8 8.8 10.4 771.3

09/01/2009 9:39 44.12 17.5 8.7 10.3 769.8

09/01/2009 9:40 43.33 17.2 8.7 10.3 765

09/01/2009 9:41 42.24 17.4 8.7 10.3 798.6

09/01/2009 9:42 41.38 17.5 8.7 10.4 799.8

09/01/2009 9:43 41.6 17.5 8.7 10.3 790.8

09/01/2009 9:44 41.19 17.7 8.7 10.4 782.5

09/01/2009 9:45 40.34 17.7 8.7 10.4 780.4

09/01/2009 9:46 39.49 17.7 8.7 10.4 774

09/01/2009 9:47 38.71 17.6 8.7 10.4 767.4

09/01/2009 9:48 37.81 17.6 8.7 10.4 774

09/01/2009 9:49 37.35 17.5 8.7 10.4 779.1

09/01/2009 9:50 36.79 17.4 8.7 10.4 773.9

09/01/2009 9:51 36.7 17.5 8.7 10.4 765.6

09/01/2009 9:52 35.78 17.4 8.7 10.4 769.3

09/01/2009 9:53 36.06 17.4 8.7 10.4 774

09/01/2009 9:54 35.91 17.5 8.7 10.3 788.8

09/01/2009 9:55 36.5 17.6 8.7 10.3 781.9

09/01/2009 9:56 37.11 17.4 8.7 10.3 777.2

09/01/2009 9:57 37.49 17.5 8.7 10.3 777.7

09/01/2009 9:58 38.03 17.4 8.7 10.4 786.3

09/01/2009 9:59 38.63 17.5 8.7 10.3 782.6

09/01/2009 10:00 38.58 17.5 8.7 10.3 787.4

09/01/2009 10:01 38.71 17.5 8.7 10.3 781.8

09/01/2009 10:02 39.33 17.3 8.7 10.4 777.2

09/01/2009 10:03 39.45 17.3 8.7 10.4 780.8

09/01/2009 10:04 40.26 17.3 8.7 10.3 778.8

09/01/2009 10:05 40.93 17.4 8.7 10.3 770.6

09/01/2009 10:06 41.03 17.3 8.7 10.3 776

09/01/2009 10:07 41.53 17.5 8.7 10.4 769.2

09/01/2009 10:08 41.71 17.3 8.7 10.3 757.9

09/01/2009 10:09 42.01 17.1 8.7 10.3 771

09/01/2009 10:10 41.69 16.7 8.7 10.3 763.3

09/01/2009 10:11 40.87 17.2 8.7 10.3 775.3

09/01/2009 10:12 40.48 17.6 8.7 10.3 779.8

Run 7

Page 13 of 16
CEMS Data

09/01/2009 10:13 40.5 17.4 8.7 10.4 784.3

09/01/2009 10:14 41.05 17.3 8.7 10.4 768.1

09/01/2009 10:15 40.94 17.1 8.7 10.4 764.9

09/01/2009 10:16 40.77 17.3 8.7 10.4 768

09/01/2009 10:17 40.6 17.3 8.7 10.3 771

09/01/2009 10:18 40.37 17.1 8.7 10.4 765

09/01/2009 10:19 40.27 17.2 8.7 10.3 772

09/01/2009 10:20 40.65 17.3 8.7 10.3 794.4

09/01/2009 10:21 40.24 17.2 8.7 10.4 775.1

09/01/2009 10:22 40.08 17.2 8.7 10.4 770.5

09/01/2009 10:23 40.07 17.1 8.7 10.4 757.8

09/01/2009 10:24 39.71 17.1 8.7 10.4 763.8

09/01/2009 10:25 39.97 17.2 8.7 10.4 764.8

09/01/2009 10:26 39.53 17.2 8.7 10.4 760.7

09/01/2009 10:27 39.34 17.4 8.8 10.4 768.6

09/01/2009 10:28 39.46 17.4 8.8 10.4 786.6

09/01/2009 10:29 39.88 17.2 8.7 10.3 779.8

09/01/2009 10:30 40.01 16.9 8.7 10.4 770.9

09/01/2009 10:31 39.83 17.3 8.8 10.4 761.7

09/01/2009 10:32 40.27 17.3 8.8 10.4 779.2

09/01/2009 10:33 40.45 17.4 8.8 10.3 776.8

09/01/2009 10:34 40.83 17.4 8.8 10.3 772.3

09/01/2009 10:35 40.68 17.1 8.8 10.3 771.6

09/01/2009 10:36 40.4 16.8 8.8 10.3 776.8

09/01/2009 10:37 40.59 16.8 8.8 10.3 776.3

40.381364 17.37 8.724 10.36 775.345455

775345.455

704039.863

Page 14 of 16
CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

09/01/2009 10:51 39.59 17.3 8.8 10.4 769.3

09/01/2009 10:52 39.96 17.3 8.8 10.4 769

09/01/2009 10:53 40.25 17.5 8.8 10.4 771.5

09/01/2009 10:54 40.37 17.5 8.8 10.4 778.5

09/01/2009 10:55 39.86 17.5 8.8 10.4 759.9

09/01/2009 10:56 39.62 17.6 8.8 10.4 775.9

09/01/2009 10:57 39.72 17.5 8.8 10.4 774

09/01/2009 10:58 39.73 17.3 8.8 10.4 773.4

09/01/2009 10:59 40.01 17.6 8.8 10.3 770

09/01/2009 11:00 39.81 17.2 8.8 10.3 768.4

09/01/2009 11:01 39.22 17.4 8.8 10.4 776.4

09/01/2009 11:02 39.93 17.4 8.8 10.3 767.8

09/01/2009 11:03 40.21 17.6 8.8 10.4 768.4

09/01/2009 11:04 40.26 17.6 8.8 10.4 768.1

09/01/2009 11:05 40.73 17.6 8.8 10.4 765.6

09/01/2009 11:06 40.95 17.5 8.8 10.4 774.2

09/01/2009 11:07 41.24 17.4 8.8 10.4 762.4

09/01/2009 11:08 41.37 17.2 8.8 10.4 760.5

09/01/2009 11:09 40.68 17.3 8.8 10.4 761.1

09/01/2009 11:10 40.63 17.4 8.8 10.4 756.4

09/01/2009 11:11 40.43 17.4 8.8 10.4 754.6

09/01/2009 11:12 40.41 17.3 8.8 10.4 759.2

09/01/2009 11:13 40.49 17.2 8.8 10.4 770.3

09/01/2009 11:14 40.03 17.3 8.8 10.3 768.7

09/01/2009 11:15 39.81 17.3 8.8 10.4 769.5

09/01/2009 11:16 39.83 17.3 8.8 10.4 773.7

09/01/2009 11:17 39.89 17.5 8.8 10.4 771.3

09/01/2009 11:18 39.69 17.3 8.8 10.4 766.5

09/01/2009 11:19 39.93 17.3 8.8 10.3 760.7

09/01/2009 11:20 40.21 17 8.8 10.4 755.2

09/01/2009 11:21 40.03 17.1 8.8 10.4 755.7

09/01/2009 11:22 40.35 17.3 8.8 10.4 770.3

09/01/2009 11:23 40.59 17.2 8.9 10.4 771.4

09/01/2009 11:24 40.68 17.4 8.9 10.4 772.3

09/01/2009 11:25 40.8 17.5 8.9 10.4 777.6

09/01/2009 11:26 40.68 17.3 8.8 10.4 777.4

09/01/2009 11:27 40.46 17.2 8.8 10.4 770.4

09/01/2009 11:28 40.34 17.3 8.8 10.4 765.2

09/01/2009 11:29 39.96 17.3 8.8 10.3 759.2

Run 8

Page 15 of 16
CEMS Data

09/01/2009 11:30 39.7 16.8 8.8 10.4 765.9

09/01/2009 11:31 39.32 17.1 8.8 10.4 766.9

09/01/2009 11:32 40.07 17.4 8.9 10.4 769.9

09/01/2009 11:33 40.05 17.3 8.8 10.4 772.8

09/01/2009 11:34 40.45 17.1 8.8 10.4 770.8

09/01/2009 11:35 40.42 17.2 8.8 10.4 763

09/01/2009 11:36 40.44 17.3 8.8 10.4 759.3

09/01/2009 11:37 40.77 17.3 8.8 10.4 767.2

09/01/2009 11:38 40.9 17.1 8.8 10.4 776.6

09/01/2009 11:39 41.05 17.2 8.8 10.4 770.3

09/01/2009 11:40 40.53 17.3 8.8 10.4 751.5

09/01/2009 11:41 40.6 17.2 8.8 10.4 759.8

09/01/2009 11:42 40.56 17.2 8.8 10.4 772.5

09/01/2009 11:43 40.93 17 8.8 10.4 776.8

09/01/2009 11:44 40.72 17.2 8.8 10.4 758.9

09/01/2009 11:45 40.63 17.2 8.8 10.4 762.3

09/01/2009 11:46 40.67 17.3 8.8 10.4 754.6

09/01/2009 11:47 40.2 17.2 8.8 10.4 750.7

09/01/2009 11:48 40.06 17.1 8.8 10.4 750.9

09/01/2009 11:49 40.49 17.1 8.8 10.4 744.8

09/01/2009 11:50 39.97 17.1 8.8 10.4 768.2

09/01/2009 11:51 40.35 17.3 8.8 10.4 776.2

09/01/2009 11:52 40.36 17.2 8.8 10.4 767.8

09/01/2009 11:53 40.37 17.2 8.8 10.3 755.5

09/01/2009 11:54 40.28 17.3 8.8 10.3 752.8

09/01/2009 11:55 39.97 16.9 8.8 10.3 762

09/01/2009 11:56 39.95 16.9 8.8 10.3 766.8

09/01/2009 11:57 40.16 17 8.7 10.3 774.3

09/01/2009 11:58 39.96 17 8.8 10.3 757

40.274706 17.28 8.804 10.38 765.972059

765972.059

704587.301

Average for test day 40.328035 17.32 8.764 10.37 770.658757

Page 16 of 16
APPENDIX E 

TEST PARTICIPANTS 
TEST PARTICIPANTS

AIR SERVICES GROUP

Scott Given Environmental Technician – Test Team Lead 

Jorge Varino Environmental Technician 

Gary Barber Environmental Technician 

Ryan Newell Environmental Technician 

Ray McDarby Senior Environmental Technician 

David A. Smith, QSTI Coordinator – Air Services Group 

Process Data

Ray McDarby Senior Environmental Technician 

Fuel Analysis

Ray McDarby Senior Environmental Technician 

Project Quality Objectives & Reporting

Ray McDarby Senior Environmental Technician 

Test Coordination

David A. Smith, QSTI Coordinator, Air Services Group 

POLK POWER STATION

Michael Perkins Environmental Coordinator 

Josh Ellwein Principal Engineer, Air Programs