# EMISSIONS TEST REPORT

POLK POWER STATION UNIT 1 FACILITY ID NUMBER: 1050233 EMISSION UNIT ID NO: -001
SULFURIC ACID MIST (SAM)

AUGUST 27 AND SE PTEMBER 1, 2009

Prepared For: Tampa Electric Company Polk Power Station P.O. Box 111 Tampa, Florida 33601-0111

Prepared By: Tampa Electric Company Environmental, Health, & Safety Air Services Group

Air Services Group 5010 Causeway Boulevard Tampa, Florida 33619- 6130

## REPORT CERTIFICATION

The sampling and subseque nt data entry/reduction detailed in this report was conducted at my direction, and I here by certify that this test report is authentic and accurate to the best of my knowledge.

Signature:__________________________ Scott E. Given Environmental Technician Test Team Lead Air Services Group Environmental Health & Safety Tampa Electric Company

I have reviewed the test performa nce, associated quality assurance activities, the resultant calculations, and the contents of this report, and certify that all project quality obj ectives have been met. Th is report is approved for submittal.

Signature:__________________________ Raymond A. McDarby, Jr. Senior Environmental Technician Quality Assurance/Quality Control Specialist Air Services Group Environmental Health & Safety Tampa Electric Company

I have reviewed the testing details and results submitted in this report, and hereby certify that this test report is authenti c and accurate to the best of my knowledge.

Signature:__________________________ David A. Smith, QSTI Coordinator – Air Services Group

Environmental Health & Safety Tampa Electric Company

## TABLE OF CONTENTS

SECTION PAGE NO. 1.0 INTRODUCTION 1
2.0 DISCUSSION OF RESULTS 2
3.0 SOURCE DESCRIPTION/TEST PROCEDURES 3
4.0 TABULATED RESULTS
SULFURIC ACID MIST TEST SUMMARY 5
NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 6
HEAT INPUT CALCULATIONS 7
5.0 STACK SAMPLING LOCATION DIAGRAM 9

APPENDICES
A. SULFURIC ACID MIST TEST INFORMATION CALCULATED RUN DATA LABORATORY ANALYSIS FIELD DATA SHEETS EQUIPMENT CALIBRATIONS

B. TURBINE DATA (PLANT INFORMATION SYSTEM)
C. FUEL ANALYSIS
D. CEMS DATA
E. TEST PARTICIPANTS

### 1 

## 1.0 INTRODUCTION

On August 27, 2009 and September 1, 2009, Tampa Electric Company’s, Environmental Services, Air Services Group per formed Sulfuric Acid Mist (SAM) source
emission tests on Unit No. 1 at the Polk Power Station. Unit No. 1 is an integrated coal gasification combined cycle (IGCC) generating unit. The combustion turbine was fired with syngas from the coal gasification system. A blend of petroleum coke and bituminous coal was gasified for this test. Testing was conducted according to United States Environmental Protection Agency (U SEPA) test methods st ipulated in 40 CFR Part 60, Appendix A and Flori da Department of Environment al Protection (FDEP)
Permit No. 1050233-016-AV.

Nitrogen Oxides (NO x 

### ) and Sulfur Dioxide (SO 2 

### ) data was taken from the Continuous Emissions Monitoring System’s (CEMS) Da ta Acquisition and Handling System (DAHS) and is presented as averages over the test period.

### 2 

## 2.0 DISCUSSION OF RESULTS

The Sulfuric Acid Mist (H 2 

### SO 4 

### ) emission rate was derived from five 1-hour test runs. The calculated average H 2 

### SO 4 

### emission rate was 39 lbs/hr. The FDEP permitted emission rate is 55 lbs/hr based on a 30-day rolling average.

Sulfur Dioxide (SO 2 

### ) emissions during the sulfuric acid mist testing were determined to
be 322 lbs/hr.

Nitrogen Oxides (NOx) emissions during the sulfuric acid mist testing were determined
to be 103 lbs/hr.

During the tests on August 27, 2009, Unit No . 1 Combustion Turbine was operated at an average load of 170 megawatts and an av erage heat input of 1697 mmBtu/hr. During the tests on September 1, 2009, Unit No. 1 Combustion Turbine was operated at an average load of 170 megawatts and an aver age heat input of 1684 mmBtu/hr. The FDEP permitted heat input is 1755 mmBtu/hr, at an ambient te mperature of 59o (corrected to 1750 mmBtu/hr based on an average inlet vane temperature of 80oF, and the manufacturer’s heat input correction curve for this unit). The calculated capacity factor during the test was 97% on August 27, 2009 and 96% on September 1, 2009.

### 3 

## 3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generat ing Station is located at County Road 630 approximately 13 miles southwest of Bartow, Po lk County, Florida. Unit No. 1 is an IGCC generating unit, with a net capacity of 192 MW when fir ed with Syngas fuel. The source sampling
location consists of a circular stack 19 feet in diameter with four sample ports located 90 degrees apart on the stack circumfe rence. A diagram of the stack sampling location is included along with other pertinent information on the test site.

Sulfuric acid mist sampling and analysi s was performed in accordance with USEPA Reference Method 8 (40 CFR Part 60, Appendix A) "Determinati on of Sulfuric Acid Mist
and Sulfur Dioxide Emissions from Stati onary Sources”, and FDEP Permit No. 1050233- 016-AV, Condition A.56. A total of eight runs were conducted during this test program. Runs 4, 5 and 6 were disqualified due to samp le contamination. These three runs were excluded because the first impinger (IPA(80% ), SO3/H2SO4 capture), gained volume. Water vapor, present in the flue gas, condens ed in the first impinger. SO2 entering the first impinger was oxidized to SO3 by t he water and trace amounts of H2O2 in the aqueous IPA solution. Flow data from the installed Continuous Emissions Monitor (CEM) was used to calculate the mass emissi ons. The flow CEM has been certified via Reference Method 2F using a 3-D flow probe to eliminate impacts of axial and nonradial flow from the measurement. The fl ow data was corrected to dry basis using the moisture number determined during the Reference Method 8 test.

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. This data was taken as 1-minute averages ov er the time frame representing the time
frame of the sulfuric acid mist test.

Plant operational data was taken from the Plant Information (PI) server system. This data was taken as 1-minute averages representi ng the time frame of the sulfuric acid mist test. Data captured included the average unit load, average fuel flow, average inlet vane temperature, and average saturator readi ngs. Details are included in Appendix B.

### 4 

## 4.0 TABULATED RESULTSAir Services GroupCustomer: Polk Power StationFacility: Unit 1Sampling Location:StackOperating Conditions:Full LoadTest Date:Run #1Run #2Run #3Run #4Run #5Run #6Run #7Run #8AverageSampled Volume, Vm(std), dscf:37.31 37.24 37.71 37.67 36.90 27.44 38.26 38.42 35.71Stack Moisture, Bwsx 100, %:5.5 6.8 6.6 12.0 11.0 7.3 9.2 8.08.2Isokinetic SamplingRate, I, %: 100.8 101.7 101.8 106.8 105.3 101.5 103.4 102.3 103.0CH2SO4,lb/dscf:5.9E-07 9.3E-07 1.3E-06 1.3E-06 1.4E-06 1.3E-06 9.6E-07 7.7E-07 1.1E-06Stack Flow (Flow CEM), dscfm: 725000 719000 721000 680000 691000 717000 704000 705000EH2SO4, lbs/hr (w/ Flow CEM):26 40 58 53 59 55 40 3345Adjusted Average (Runs 4, 5, and 6 excluded): 39EH2SO4, is calculated as CH2SO4, lbs/dscf times Stack Flow (Flow CEM), dscfm times 60 minutes/hour.Stack Flow (Flow CEM), dscfm is Stack Flow from DAHScorrected to the Reference Method 8 measured moisture.Sulfuric Acid Mist - Reference Method 840 CFR 60, Appendix A - Test MethodsReference Method 8Test SummaryAugust 27, 2009September 1, 20095

## POLK POWER STATIO N N O X 

## & S O 2 

## COMPLIANCE DATA FROM CEM S

NO x 

### SO 2 

### Flow NO x 

### SO 2 

### ppmvw ppmvw kscfmw lbs/hr lbs/hr

20.1 43.5 771 111 334

NO x 

### SO 2 

### Flow NO x 

### SO 2 

### ppmvw ppmvw kscfmw lbs/hr lbs/hr

17.3 40.3 771 95.6 309 

### Test Average: 103 322 NOX, lbs/hr calculated as: NOX, ppmvw x 1.194E-07 x Flow, kscfmw x 60 min/hr x 1000/k

SO2, lbs/hr calculated as: SO2, ppmvw x 1.660E-07 x Flow, kscfmw x 60 min/hr x 1000/k 

### September 1, 2009

CEM Data Calculated Data

HEAT RECOVERY STEAM GENERATO R UNIT 1 Au g ust 27, 2009

CEM Data Calculated Data

6

## POLK POWER STATIO N HEAT INPUT CALCULATIO N

Average fuel flow: 6529 Kcfh Mole weight correction to meter ca l: 0.9883 mole weight correction factor Corrected fuel flow:1 6453 Kc fh, corrected for density Average moisture: 0.28 % H 2 

### 0 added to fuel
Corrected fuel flow:2 6435 Kscf h, corrected for moisture Gross heating value of fuel (HHV): 263.7 Btu/scf Heat Input: 1697 mmBtu/hr

Average fuel flow: 6587 Kcfh Mole weight correction to meter ca l: 0.9883 mole weight correction factor Corrected fuel flow:1 6510 Kc fh, corrected for density Average moisture: 1.93 % H 2 

### 0 added to fuel
Corrected fuel flow:2 6385 Kscf h, corrected for moisture Gross heating value of fuel (HHV): 263.7 Btu/scf Heat Input: 1684 mmBtu/hr

Mole weight correction factor to meter calibration is taken from ratio of syngas mole weight to calibra tion gas mole weight. 

### September 1, 2009

Average fuel flow from Plant Information Data Base. 

### COMBINED CYCLE COMBUSTION TURBINE UNIT 1 Au g ust 27, 2009

1Average fuel flow times mo le weight correction factor. 2Corrected fuel flow times (1 - (Average moisture / 100)).

Gross Heating value of fuel (HHV) is from fuel analysis. Heat input is (HHV x Corrected fuel flow) / 1000.

7

### 8 

## 5.0 SAMPLING LOCATION TRAVERSE DIAGRAM

### 9 UNFIRED HEAT

RECOVERY

BOILER TRANSITION

DUCT

EXHAUST FROM TURBINE 14 FT.

38 FT. 150 FT.

136 FT.

PORT LOCATION PLAN 19.0 FT.ID.

STACK DIAMETERS DOWNSTREAM FROM DISTURBANCE = 2.0 STACK DIAMETERS UPSTREAM FROM DISTURBANCE = 0.7 STACK DIAMETER = 19.0 FT. STACK AREA = 283.529 SQ. FT. STACK AREA =40828.138 SQ. IN.

TRAVERSE POINTS 1 - 4.79 ” 2 - 15.28 ” 3 - 26.90 ” 4 - 40.36 ” 5 - 57.00 ” 6 - 80.17 ”

ADD 13” PORT LENGTH TO POINTS



### Polk Power Station
Unit No. 1
IGCC
Test Location

## APPENDIX A

SULFURIC ACID MIST TEST INFORMATION

### CALCULATED RUN DATA

### Air Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 1 Date: 08/27/2009

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.196 inches Barometric Pressure, P b : 29.80 "Hg Nozzle Area, A n : 0.00020951 ft 2
Stack Pressure, P s : 29.74 "Hg Average Orifice Meter, Δ H: 1.288 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 37.623 ft 3
Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 70.9 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 327.8 o F
10.5 % O 2 Average √Δ p: 1.139 "H 2 O

0.0 % CO Condensate Volume, V lc : 45.7 ml
80.5 % N 2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 2.154 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 37.310 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.055 %
FDA = 1.0 - B ws 0.945 %
M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.86 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 29.21 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 60) 100.8 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0102 Volume Titrant Blank, V tb 0.85 Volume Titrant Sample, V t 4.85 Volume of Sample Aliquot, V a 50 Total Volume of Solution, V soln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 5.911E-07 lb/dscf Stack Flow (Flow CEM), dscfm: 725000 dscfm
E H2SO4 = C H2SO4 x Stack Flow x 60 = 26 lb/hr

### Air Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 2 Date: 08/27/2009

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.196 inches Barometric Pressure, P b : 29.81 "Hg Nozzle Area, A n : 0.00020951 ft 2
Stack Pressure, P s : 29.75 "Hg Average Orifice Meter, Δ H: 1.291 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 37.591 ft 3
Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 71.7 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 327.5 o F
10.5 % O 2 Average √Δ p: 1.139 "H 2 O

0.0 % CO Condensate Volume, V lc : 57.2 ml
80.5 % N 2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 2.696 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 37.235 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.068 %
FDA = 1.0 - B ws 0.932 %
M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.86 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 29.06 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 101.7 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0102 Volume Titrant Blank, V tb 0.85 Volume Titrant Sample, V t 7.1 Volume of Sample Aliquot, V a 50 Total Volume of Solution, V soln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 9.254E-07 lb/dscf Stack Flow (Flow CEM), dscfm: 719000 dscfm
E H2SO4 = C H2SO4 x Stack Flow x 60 = 40 lb/hr

### Air Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 3 Date: 08/27/2009

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.196 inches Barometric Pressure, P b : 29.81 "Hg Nozzle Area, A n : 0.00020951 ft 2
Stack Pressure, P s : 29.75 "Hg Average Orifice Meter, Δ H: 1.318 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.095 ft 3
Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 72.1 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 328.8 o F
10.5 % O 2 Average √Δ p: 1.152 "H 2 O

0.0 % CO Condensate Volume, V lc : 56.4 ml
80.5 % N 2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 2.659 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 37.710 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.066 %
FDA = 1.0 - B ws 0.934 %
M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.86 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 29.08 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 101.8 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0102 Volume Titrant Blank, V tb 0.85 Volume Titrant Sample, V t 10 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 1.338E-06 lb/dscf Stack Flow (Flow CEM), dscfm: 721000 dscfm
E H2SO4 = C H2SO4 x Stack Flow x 60 = 58 lb/hr

### A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 4 Date: 08/27/2009

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.196 inches Barometric Pressure, P b : 29.81 "Hg Nozzle Area, A n : 0.00020951 ft 2
Stack Pressure, P s : 29.75 "Hg Average Orifice Meter, Δ H: 1.314 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 37.986 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 71.2 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 330.3 o F
10.5 % O 2 Average √ Δ p: 1.152 "H 2 O

0.0 % CO Condensate Volume, V lc : 108.8 ml
80.5 % N 2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 5.129 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 37.667 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.120 % FDA = 1.0 - B ws 0.880 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.86 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 28.44 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s 106.8 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0102 Volume Titrant Blank, V tb 0.95 Volume Titrant Sample, V t 9.8 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 1.295E-06 lb/dscf Stack Flow (Flow CEM), dscfm: 680000 dscfm E H2SO4 = C H2SO4 x Stack Flow x 60 = 53 lb/hr

### A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 5 Date: 08/27/2009

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.196 inches Barometric Pressure, P b : 29.80 "Hg Nozzle Area, A n : 0.00020951 ft 2
Stack Pressure, P s : 29.77 "Hg Average Orifice Meter, Δ H: 1.264 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 37.270 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 71.8 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 331.0 o F
10.5 % O 2 Average √ Δ p: 1.131 "H 2 O

0.0 % CO Condensate Volume, V lc : 92.8 ml
80.5 % N 2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 4.375 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 36.900 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.106 % FDA = 1.0 - B ws 0.894 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.86 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 28.60 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s 105.3 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0102 Volume Titrant Blank, V tb 0.95 Volume Titrant Sample, V t 10.4 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 1.412E-06 lb/dscf Stack Flow (Flow CEM), dscfm: 691000 dscfm E H2SO4 = C H2SO4 x Stack Flow x 60 = 59 lb/hr

### A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 6 Date: 08/27/2009

Sample Time, θ : 45 minutes Nozzle Diameter, D n : 0.196 inches Barometric Pressure, P b : 29.75 "Hg Nozzle Area, A n : 0.00020951 ft 2
Stack Pressure, P s : 29.69 "Hg Average Orifice Meter, Δ H: 1.263 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 27.730 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 71.2 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 330.6 o F
10.5 % O 2 Average √ Δ p: 1.130 "H 2 O

0.0 % CO Condensate Volume, V lc : 46.0 ml
80.5 % N 2 Meter Box Y: 0.998 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 2.168 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 27.436 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.073 % FDA = 1.0 - B ws 0.927 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.86 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 28.99 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s 101.5 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0102 Volume Titrant Blank, V tb 0.95 Volume Titrant Sample, V t 7.35 Volume of Sample Aliquot, V a 50 Total Volume of Solution, V soln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 1.286E-06 lb/dscf Stack Flow (Flow CEM), dscfm: 717000 dscfm E H2SO4 = C H2SO4 x Stack Flow x 60 = 55 lb/hr

### A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 7 Date: 09/01/2009

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.198 inches Barometric Pressure, P b : 29.80 "Hg Nozzle Area, A n : 0.00021381 ft 2
Stack Pressure, P s : 29.74 "Hg Average Orifice Meter, Δ H: 1.397 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.080 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 71.0 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 325.1 o F
10.5 % O 2 Average √ Δ p: 1.151 "H 2 O

0.0 % CO Condensate Volume, V lc : 82.2 ml
80.5 % N 2 Meter Box Y: 1.011 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 3.875 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 38.259 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.092 % FDA = 1.0 - B ws 0.908 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.86 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 28.77 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s 103.4 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0099 Volume Titrant Blank, V tb 0.01 Volume Titrant Sample, V t 6.85 Volume of Sample Aliquot, V a 50 Total Volume of Solution, V soln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 9.566E-07 lb/dscf Stack Flow (Flow CEM), dscfm: 704000 dscfm E H2SO4 = C H2SO4 x Stack Flow x 60 = 40 lb/hr

### A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 8 Date: 09/01/2009

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.198 inches Barometric Pressure, P b : 29.81 "Hg Nozzle Area, A n : 0.00021381 ft 2
Stack Pressure, P s : 29.75 "Hg Average Orifice Meter, Δ H: 1.410 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.220 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 71.0 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 325.0 o F
10.3 % O 2 Average √ Δ p: 1.156 "H 2 O

0.0 % CO Condensate Volume, V lc : 71.0 ml
80.7 % N 2 Meter Box Y: 1.011 dimensionless

Data Calculated from Source Measurements:
V w(std) = 4.714E-02 x V lc 3.347 scf
V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 38.417 dscf
B ws = V w(std) / (V m(std) + V w(std) ) 0.080 % FDA = 1.0 - B ws 0.920 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.85 lb./lb. mole
M s = (M d x FDA) + (18.0 x B ws ) 28.90 lb./lb. mole I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s 102.3 %

Data from Laboratory Analysis: H 2 SO 4 /SO 3 Normality of Barium Chloride titrant, N 0.0099 Volume Titrant Blank, V tb 0.01 Volume Titrant Sample, V t 5.55 Volume of Sample Aliquot, V a 50 Total Volume of Solution, V soln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 7.716E-07 lb/dscf Stack Flow (Flow CEM), dscfm: 705000 dscfm E H2SO4 = C H2SO4 x Stack Flow x 60 = 33 lb/hr

### LABORATORY ANALYSIS

## Laboratory Services
5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272 Report For: 

## Laboratory ID: AB02584

Date and Time Collected: Sampled By: 

### Sample Information Description: 

### Location Code: 10/6/2009 Report Date:

Polk Unit 1 SO2 Engineering Test 

### TE_PK_1_SO2ENGINEERING

Project Account Code: 8/28/2009 Date of Sample Receipt: Sample Collection Method: 

### Laboratory Results 8/27/2009 12:00:00 AM

Result PARAMETER Qualifier Code Test

Method Analyst Units Upper Limit MDL Violation Check Analysis Date & Time Lower

Limit Normality of BaCl2 * 2H2O 0.0001 KARXL 0.0103 8/31/2009 2:30:00 PM
SO2, Avg. of Blank Titrations milliliters 0.1 EPA Method 6 KARXL 0.01 8/31/2009 2:30:00 PM
SO2, Final Sample Volume milliliters 0.1 EPA Method 6 KARXL see comment 8/31/2009 2:30:00 PM
SO2, Run 1, Avg. of Titrations milliliters 0.01 EPA Method 6 KARXL 15.25 8/31/2009 2:30:00 PM
SO2, Run 2, Avg. of Titrations milliliters 0.01 EPA Method 6 KARXL 14.55 8/31/2009 2:30:00 PM
SO2, Run 3, Avg. of Titrations milliliters 0.01 EPA Method 6 KARXL 16.10 8/31/2009 2:30:00 PM
SO2, Run 4, Avg. of Titrations milliliters 0.01 EPA Method 6 KARXL 15.40 8/31/2009 2:30:00 PM
SO2, Run 5, Avg. of Titrations milliliters 0.01 EPA Method 6 KARXL 13.80 8/31/2009 2:30:00 PM
SO2, Run 6, Avg. of Titrations milliliters 0.01 EPA Method 6 KARXL 10.00 8/31/2009 2:30:00 PM
SO2, Volume of Sample Aliquot milliliters 0.1 EPA Method 6 KARXL see comment 8/31/2009 2:30:00 PM 

### Comments

Designee for Peggy Penner, Manager, Laboratory Services All results calculated on a wet to wet basis, unless otherwise indicated. Runs 1, 2, 3, 4, 5 and the field blank have final sample volumes of 500ml. Run 6 has a final sample volume of 250ml. Runs 1, 2, 3, 4, 5 and the field blank all have sample aliquots of 20ml. Run 6 has a sample aliquot of 10ml.
Should there be any questions regarding this report, please contact:

(813) 630-7490 Cheryl Howard,

Report Number: Page 1 of 1 "General Report"

AB02584-100609-09 Laboratory Services certifies that the test results in this report meet all requirements of the NELAC standards, unless indicated otherwise in the body of the report. Unless otherwise noted, all methods followed are per the most current published version of 40 CFR Part 136, Table B. Results reported on this report pertain to the above referenced sample only.

## Laboratory Services
5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272 Report For: 

## Laboratory ID: AB02640

Date and Time Collected: Sampled By: 

### Sample Information

JORGE VARINO Description: 

### Location Code: 10/6/2009 Report Date:

Polk Unit 1 SO3 Engineering Test 

### TE_PK_1_SO3ENGINEERING

Project Account Code: 9/2/2009 Date of Sample Receipt: Sample Collection Method: 

### Laboratory Results 9/1/2009 12:00:00 PM

Result PARAMETER Qualifier Code Test

Method Analyst Units Upper Limit MDL Violation Check Analysis Date & Time Lower

Limit Normality of BaCl2 * 2H2O 0.0001 KARXL 0.0099 9/2/2009 10:30:00 AM
SO3, Avg. of Blank Titrations milliliters 0.01 EPA - Meth.8 KARXL 0.01 I 9/2/2009 10:30:00 AM
SO3, Run #1, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 6.85 9/2/2009 10:30:00 AM
SO3, Run #2, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 5.55 9/2/2009 10:30:00 AM
SO3, Volume of Contained Sample milliliters 1 EPA - Meth.8 KARXL 250 9/2/2009 10:30:00 AM
SO3, Volume of Sample Aliquot milliliters 0.1 EPA - Meth.8 KARXL 50 9/2/2009 10:30:00 AM



### Comments

Designee for Peggy Penner, Manager, Laboratory Services I - The reported value is between the laboratory method detection limit (MDL) and the laboratory practical quantitation limit (PQL). PQL = 4 x MDL. All results calculated on a wet to wet basis, unless otherwise indicated. Data Qualifier Codes Explanation:

Should there be any questions regarding this report, please contact:

(813) 630-7490 Cheryl Howard,

Report Number: Page 1 of 1 "General Report"

AB02640-100609-09 Laboratory Services certifies that the test results in this report meet all requirements of the NELAC standards, unless indicated otherwise in the body of the report. Unless otherwise noted, all methods followed are per the most current published version of 40 CFR Part 136, Table B. Results reported on this report pertain to the above referenced sample only.

### FIELD DATA SHEETS

### EQUIPMENT CALIBRATIONS

### A ir Services Grou p



## SUMMARY OF E Q UIPMENT CALIBRATION S

EQUIPMENT CAL DATE METHOD RESULTS

CONSOLE (MB 06) USEPA RM 5 INITIA L 08/04/2009 (ORIFICE) 0.998 POST TEST 08/31/2009 0.998

CONSOLE (MB 08) USEPA RM 5 INITIA L 08/04/2009 (ORIFICE) 1.011 POST TEST 09/18/2009 1.010

NOZZLE (SN06) CALIPER INITIA L 08/03/2009 MEASUREMENTS 0.196 POST TEST 08/28/2009 0.195

NOZZLE (SN16) CALIPER INITIA L 08/03/2009 MEASUREMENTS 0.198 POST TEST 09/03/2009 0.198

PYROMETER (PY 10) 08/04/2009 ASTM THERMOMETER + 2 o 

### F

PYROMETER (PY 20) 08/04/2009 ASTM THERMOMETER + 2 o 

### F

PITOT TUBE (PT 11) 08/04/2009 USEPA RM 2 C p 

### = 0.84

PITOT TUBE (PT 12) 08/04/2009 USEPA RM 2 C p 

### = 0.84

BAROMETER (BR 06) 08/07/2009 NWS COMPARISON + 0.01" Hg

### Environmental Services Air Services Group

Red Team Manufacturer: Thermo Anderson Calibration Date: Model Number:MST-C1 Barometric Pressure: 30.07 "Hg Instrument Code Number: ^MB06 Theoretical Critical Vacuum: 14.18 "Hg LabWorks Sample Number: Calibrated By:

Initial Final Total Δ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes ft 3 

### ft 3 

### ft 3 

### oF oF oF oF 1.95 15 372.800 384.439 11.639 66 71 64 71 1.20 15 384.439 393.437 8.998 70 72 70 74 0.62 15 393.437 400.173 6.736 74 75 74 77 3.60 15 400.173 416.022 15.849 69 77 60 76

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 63 0.5923 19.5 70 70 70.0 55 0.4596 21.0 70 70 70.0 48 0.3452 23.0 70 70 70.0 73 0.8106 16.0 70 70 70.0

Dry Gas Meter Calibration Calibration Volume Volume Volume Y Δ H α Corrected Corrected Nominal Value QA/QC Value QA/QC
Vm (std) , ft 3 Vcr (std) , ft 3 Vcr (std) , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2

11.748 11.605 11.595 0.988 -0.010 1.842 0.037 9.006 9.005 8.997 1.000 0.002 1.870 0.065 6.689 6.763 6.758 1.011 0.013 1.701 -0.104 15.987 15.882 15.869 0.993 -0.005 1.807 0.002 Averages: 0.998 1.805 

### USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method Quarterly Calibration

08/04/2009

SEG

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. The Critical Orifice Coefficient, K', should be in English units. 

### IMPORTANT Dry Gas Meter Readings Initial Temperatures Final Tempertures

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02. For Calibration Δ H α , the acceptable tolerance of individual values from the average is + 0.2. 

### Critical Orifice Readings Ambient Temperatures

CALCULATED DATA Critical Orifice

### Environmental Services Air Services Group

Manufacturer: Thermo Calibration Date: Model Number:MST Barometric Pressure: 29.99 "Hg Instrument Code Number: MB06 Theoretical Critical Vacuum: 14.15 "Hg LabWorks Sample Number: Calibrated By: A ssociated Test: Team: RED

Initial Final Total Δ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes ft 3 

### ft 3 

### ft 3 

### oF oF oF oF

1.2 10 778.000 784.000 6.000 69 74 69 74 1.2 10 784.000 790.010 6.010 69 74 69 75 1.2 10 790.010 796.025 6.015 69 75 69 75

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 55 0.4596 21.0 71 71 71.0 55 0.4596 21.0 71 71 71.0 55 0.4596 21.0 71 71 71.0

Dry Gas Meter Calibration Calibration Volume Volume Volume Y Δ H α Corrected Corrected Nominal Value QA/QC Value QA/QC
Vm (std) , ft 3 Vcr (std) , ft 3 Vcr (std) , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2

5.990 5.981 6.004 0.999 0.001 1.879 0.001 5.997 5.981 6.004 0.997 0.000 1.878 0.000 5.999 5.981 6.004 0.997 -0.001 1.877 -0.001 Averages: 0.998 1.878 Prior Y: 0.998 % Difference:(+/-5%) 0.03% PASS CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02. For Calibration Δ H α , the acceptable tolerance of individual values from the average is + 0.2. 

### Critical Orifice 

### USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

RJN 08/31/2009 

### POST - TEST CALIBRATION CHECK

Ambient Temperatures Dry Gas Meter Readings Final Tempertures Initial Temperatures

Critical Orifice Readings IMPORTANT

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. The Critical Orifice Coefficient, K', should be in English units.

### Environmental Services Air Services Group

Blue Team Manufacturer: APEX Calibration Date: Model Number: 522 Barometric Pressure: 30.07 "Hg Instrument Code Number: ^MB08 Theoretical Critical Vacuum: 14.18 "Hg LabWorks Sample Number: Calibrated By:

Initial Final Total Δ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes ft 3 

### ft 3 

### ft 3 

### oF oF oF oF 0.70 15 786.800 793.426 6.626 68 68 68 68 3.60 15 793.426 809.011 15.585 69 69 72 72 2.00 15 809.011 820.463 11.452 71 71 72 72 1.20 15 820.463 829.370 8.907 72 72 72 72

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 48 0.3452 22.0 70 70 70.0 73 0.8106 17.0 70 70 70.0 63 0.5923 19.0 70 70 70.0 55 0.4596 21.0 70 70 70.0

Dry Gas Meter Calibration Calibration Volume Volume Volume Y Δ H α Corrected Corrected Nominal Value QA/QC Value QA/QC
Vm (std) , ft 3 Vcr (std) , ft 3 Vcr (std) , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2

6.668 6.763 6.758 1.014 0.003 1.946 0.072 15.720 15.882 15.869 1.010 -0.001 1.807 -0.068 11.485 11.605 11.595 1.010 -0.001 1.877 0.002 8.907 9.005 8.997 1.011 -0.001 1.868 -0.006 Averages: 1.011 1.875 

### USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method Quarterly Calibration

08/04/2009

SEG

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. The Critical Orifice Coefficient, K', should be in English units. 

### IMPORTANT Dry Gas Meter Readings Initial Temperatures Final Tempertures

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02. For Calibration Δ H α , the acceptable tolerance of individual values from the average is + 0.2. 

### Critical Orifice Readings Ambient Temperatures

CALCULATED DATA Critical Orifice

### Environmental Services Air Services Group

Manufacturer: Apex Calibration Date: Model Number: 522 Barometric Pressure: 29.98 "Hg Instrument Code Number: mb08 Theoretical Critical Vacuum: 14.14 "Hg LabWorks Sample Number: Calibrated By: A ssociated Test: Team: RED

Initial Final Total Δ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes ft 3 

### ft 3 

### ft 3 

### oF oF oF oF

1.2 10 437.300 443.215 5.915 69 69 69 69 1.2 10 443.215 449.125 5.910 69 69 70 70 1.2 10 449.125 455.040 5.915 70 70 71 71

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 55 0.4596 21.0 71 71 71.0 55 0.4596 21.0 71 71 71.0 55 0.4596 21.0 71 71 71.0

Dry Gas Meter Calibration Calibration Volume Volume Volume Y Δ H α Corrected Corrected Nominal Value QA/QC Value QA/QC
Vm (std) , ft 3 Vcr (std) , ft 3 Vcr (std) , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2

5.931 5.979 6.004 1.008 -0.002 1.888 0.002 5.920 5.979 6.004 1.010 0.000 1.886 0.001 5.914 5.979 6.004 1.011 0.001 1.883 -0.003 Averages: 1.010 1.886 Prior Y: 1.011 % Difference:(+/-5%) 0.12% PASS BB-st4-ecotherm-(09-17-09) IMPORTANT

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. The Critical Orifice Coefficient, K', should be in English units.



### Ambient Temperatures Dry Gas Meter Readings Final Tempertures Initial Temperatures

Critical Orifice Readings 

### USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

SEG 09/18/2009 

### POST - TEST CALIBRATION CHECK

CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02. For Calibration Δ H α , the acceptable tolerance of individual values from the average is + 0.2. 

### Critical Orifice

### Environmental Service s A ir Services Grou p

Shared Resource

Calibration Date: Responsible Party:

Nozzle Maximum 

### Average

I.D. D 1 

### D 2 

### D 3 Difference, " 

### D n 

### , inches
^SN01 0.114 0.117 0.114 0.003 0.115 ^SN04 0.127 0.127 0.127 0.000 0.127 ^SN05 0.150 0.150 0.149 0.001 0.150 ^SN06 0.195 0.197 0.196 0.002 0.196 ^SN10 0.299 0.300 0.299 0.001 0.299 ^SN12 0.388 0.386 0.387 0.002 0.387 ^SN15 0.164 0.164 0.164 0.000 0.164 ^SN16 0.197 0.198 0.198 0.001 0.198 ^SN19 0.280 0.281 0.279 0.002 0.280 ^SN22 0.369 0.369 0.369 0.000 0.369 ^SN30 0.314 0.313 0.314 0.001 0.314 ^SN36 0.187 0.187 0.188 0.001 0.187 ^SN37 0.206 0.207 0.206 0.001 0.206 ^SN38 0.249 0.251 0.249 0.002 0.250 ^SN46 0.190 0.190 0.189 0.001 0.190 ^SN47 0.202 0.201 0.202 0.001 0.202 ^SN48 0.251 0.251 0.250 0.001 0.251 ^SN50 0.311 0.313 0.313 0.002 0.312 ^SN58 0.240 0.242 0.242 0.002 0.241 ^SN68 0.246 0.247 0.247 0.001 0.247 ^SN69 0.376 0.376 0.376 0.000 0.376 ^SN70 0.616 0.616 0.615 0.001 0.616 ^SN71 0.613 0.614 0.613 0.001 0.613 ^SN72 0.377 0.377 0.377 0.000 0.377 ^SN73 0.502 0.501 0.502 0.001 0.502 ^SN74 0.485 0.485 0.482 0.003 0.484 ^SN75 0.211 0.210 0.211 0.001 0.211 ^SN76 0.249 0.249 0.248 0.001 0.249 ^SN77 0.273 0.272 0.272 0.001 0.272 

### Nozzle Diameter, D n 

### (in) QUARTERLY NOZZLE CALIBRATIONS

STEEL NOZZLE SET

08/03/2009 SEG

### Environmental Service s A ir Services Grou p

Shared Resource Calibration Date: Calibration Personnel: Test Designation:

Maximum 

### Average D 1 

### D 2 

### D 3 Difference, " 

### D n 

### , inches
0.195 0.195 0.196 0.001 0.195

Data Notations: Maximum Difference must be < 0.004".



### Quarterly (pre-test) value for nozzle ID SN06 was 0.196

Difference (Pre-test/Post-test) is: 0.001 PASS SN06 POST TEST NOZZLE CALIBRATION

Nozzle Identifier Nozzle Diameter, D n 

### (in) 08/28/2009 SEG Polk 1 RM8 (08/27/09)

### Environmental Service s A ir Services Grou p

Shared Resource Calibration Date: Calibration Personnel: Test Designation:

Maximum 

### Average D 1 

### D 2 

### D 3 Difference, " 

### D n 

### , inches
0.197 0.198 0.198 0.001 0.198

Quarterly (pre-test) value for nozzle ID SN 16 was 0.198

Difference (Pre-test/Post-test) is: 0.000 SN 16 POST TEST NOZZLE CALIBRATION

Nozzle Identifier Nozzle Diameter, D n 

### (in) 03-Sep-09 McDarby Polk SAM (1-Sep-2009)

### Environmental Services A ir Services Group

Red Team Pyrometer Under Tes t Pyrometer Number: ^PY10 Labworks Sample # Calibration Date: 08/04/2009

Calibrator Information Calibrator Type/Manufacturer: Hart Scientific Calibrator Serial Number: A OA024 Date of Last Calibration: 04/29/2009 Calibration Personnel (Typed and Signature):

Calibration Data

Calibration Reference Pyrometer Point Temperature Indication Difference

1 

### 400 401 -1 2 

### 212 210 2 3 

### 32 31 1

Reference temperatures must encompass the expected range of measurement. These three points should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit. Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration Point Difference

1 

### Pass 2 

### Pass 3 

### Pass 0

SEG Pyrometer Calibration

### A ir Services Group

Shared Pyrometer Under Tes t Pyrometer Number: ^PY20 Labworks Sample # Calibration Date: 08/04/2009

Calibrator Information Calibrator Type/Manufacturer: Hart Scientific Calibrator Serial Number: A OA024 Date of Last Calibration: 04/29/2009 Calibration Personnel (Typed and Signature):

Calibration Data

Calibration Reference Pyrometer Point Temperature Indication Difference

1 

### 400 400 0 2 

### 212 212 0 3 

### 32 30 2

Reference temperatures must encompass the expected range of measurement. These three points should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit. Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration Point Difference

1 

### Pass 2 

### Pass 3 

### Pass N/ A

SEG

Pyrometer Calibration

### Pitot Tube ID # Calibration Date Operating Quarter/Year: 3/09 Openings Damaged? ___ Y

_ _

_ N Repaired?

_ __ _ Y ___ N ___ N/A

Labworks #:

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 0.5 degrees Dt 0.48 < Dt > 0.95 cm

α 2 0.2 degrees α < 10 degrees β 1 0.5 degrees β 2 1 degrees β 1 < 5 degrees (alongside top impact openings) Gamma, Theta, Α

, Ζ

, and W Determination s β 2 < 5 degrees (alongside bottom impact openings)

ψ 0 degrees Ζ < 0.32 cm ( Α sin ψ )
Α 2.35 cm W < 0.08 cm (Asin ο )
Ζ 0.000 cm Α distance between tips

ο angle of plane on side of pitots

ο 0.6 degrees ψ angle between tips
W 0.025 cm



### Comments:

Calibrated by: RJN

details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems: Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.



### REMOVABLE Pass

NOTES All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement 

### Pass Pass ( α 1 measured across top impact openings) 

### Pass ( α 2 measured across bottom impact openings) 

### Shared Resource

#REF!

Pass Pass PITOT TUBE CALIBRATION DATA SHEET

PT11

08/04/2009

### Pitot Tube ID # Calibration Date Operating Quarter/Year: 3/09 Openings Damaged? ___ Y

_ _

_ N Repaired?

_ __ _ Y ___ N ___ N/A

Labworks #:

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 0.3 degrees Dt 0.48 < Dt > 0.95 cm

α 2 0 degrees α < 10 degrees β 1 0 degrees β 2 0 degrees β 1 < 5 degrees (alongside top impact openings) Gamma, Theta, Α

, Ζ

, and W Determination s β 2 < 5 degrees (alongside bottom impact openings)

ψ 0.1 degrees Ζ < 0.32 cm ( Α sin ψ )
Α 2.26 cm W < 0.08 cm (Asin ο )
Ζ 0.004 cm Α distance between tips

ο angle of plane on side of pitots

ο 0.8 degrees ψ angle between tips
W 0.032 cm



### Comments:

Calibrated by: PITOT TUBE CALIBRATION DATA SHEET

PT12

08/04/2009 

### Shared Resource

Pass Pass Pass ( α 1 measured across top impact openings) 

### Pass ( α 2 measured across bottom impact openings)



### Pass

Pass

NOTES All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems: Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.



### REMOVABLE

RJN

### Air Services Group

Blue Team Instrument Number: Calibration Date: Calibration Personnel: Labworks #: Difference T ime "H g 10:05 0.01 11:07 0 12:10 -0.01

Avera g e Difference: 0

Note: Barometric readin g s must a g ree within ± 0.1 "H g

. Current Reference is National Weather Service, TIA.
Comments (Note any ad j ustments): Current Conditions at Tampa International Airport 30.11 30.12 30.10 30.09 30.11 30.11 Barometer Readin g Reference Readin g Inches Mercury Inches Mercury BAROMETER CALIBRATION

^BR06 08/07/2009 SEG

## APPENDIX B

TURBINE DATA

### Plant Information Database Query

Plant Information Source: polk-1pisrv Start Time: 08/27/2009 8:47

End Time: 08/27/2009 18:35 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 170.0800835 6529.01782 80.8572231 0.27653345 27-Aug-09 08:47:00 170.5224762 6545.80859 78.9909134 0.27560338 27-Aug-09 08:48:00 170.0342102 6534.49072 78.9317551 0.27562886 27-Aug-09 08:49:00 170.3021851 6548.9834 78.46978 0.27565435 27-Aug-09 08:50:00 170.8650208 6557.11475 78.6237717 0.27567983 27-Aug-09 08:51:00 170.7047882 6552.53125 78.7777634 0.27570531 27-Aug-09 08:52:00 170.1927948 6558.82568 78.9317551 0.27573079 27-Aug-09 08:53:00 170.2024384 6551.73633 79.0248108 0.27575627 27-Aug-09 08:54:00 170.4185791 6549.90332 78.7676239 0.27578175 27-Aug-09 08:55:00 170.956192 6571.29297 78.9228897 0.27580723 27-Aug-09 08:56:00 171.0022736 6558.09277 78.7589264 0.27583271 27-Aug-09 08:57:00 169.8847809 6523.62451 78.8613052 0.27585819 27-Aug-09 08:58:00 169.1328278 6509.07959 78.9636917 0.27588367 27-Aug-09 08:59:00 169.5056915 6504.49609 79.0660706 0.27590916 27-Aug-09 09:00:00 170.3726501 6524.96875 79.168457 0.27593464 27-Aug-09 09:01:00 169.756073 6499.5459 79.2708359 0.27596012 27-Aug-09 09:02:00 169.0185242 6498.32373 79.3732224 0.2759856 27-Aug-09 09:03:00 169.5222778 6523.80811 79.6308517 0.27601108 27-Aug-09 09:04:00 169.5581055 6515.19092 79.4142761 0.27603656 27-Aug-09 09:05:00 169.5939331 6514.21289 79.5132599 0.27606204 27-Aug-09 09:06:00 170.095871 6543.91406 79.6660004 0.27608752 27-Aug-09 09:07:00 170.6277618 6529.00244 79.4348068 0.276113 27-Aug-09 09:08:00 170.1584625 6524.35791 79.6243515 0.27613848 27-Aug-09 09:09:00 169.5267334 6516.04639 79.9255905 0.27616397 27-Aug-09 09:10:00 169.0944977 6510.17969 79.7624893 0.27618945 27-Aug-09 09:11:00 168.9771271 6511.09619 79.9206085 0.27621493 27-Aug-09 09:12:00 169.0254669 6521.72314 79.8202515 0.27624041 27-Aug-09 09:13:00 169.7894135 6556.41895 79.7198944 0.27626589 27-Aug-09 09:14:00 171.0684662 6556.13672 80.1036758 0.27629137 27-Aug-09 09:15:00 171.6353607 6551.61426 80.2576675 0.27631685 27-Aug-09 09:16:00 171.1860962 6545.01416 80.4116592 0.27634233 27-Aug-09 09:17:00 170.6072388 6528.88037 80.5656509 0.27636781 27-Aug-09 09:18:00 169.6759338 6520.08008 80.4989243 0.27639329 27-Aug-09 09:19:00 169.181488 6525.94678 80.2480698 0.27641878 27-Aug-09 09:20:00 169.8589172 6537.31396 80.1465149 0.27644426



### Page 1 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 09:21:00 169.9703979 6545.74756 80.04496 0.27646974 27-Aug-09 09:22:00 169.4836273 6478.79102 80.1019669 0.27649522 27-Aug-09 09:23:00 169.0652008 6500.35254 80.3072891 0.2765207 27-Aug-09 09:24:00 170.7176208 6555.52783 80.5126114 0.27654618 27-Aug-09 09:25:00 170.2809448 6533.6792 80.6695099 0.27657166 27-Aug-09 09:26:00 170.6240387 6533.98975 80.7710648 0.27659714 27-Aug-09 09:27:00 170.0044708 6522.51855 80.8726196 0.27662262 27-Aug-09 09:28:00 171.4468079 6560.45117 80.8171768 0.2766481 27-Aug-09 09:29:00 171.0215302 6552.71436 80.6671371 0.27667359 27-Aug-09 09:30:00 169.7569733 6516.74658 80.7899323 0.27669907 27-Aug-09 09:31:00 170.8825989 6537.28955 80.9127274 0.27672455 27-Aug-09 09:32:00 169.368988 6502.0249 81.0355225 0.27675003 27-Aug-09 09:33:00 167.7615051 6480.96143 81.1583099 0.27677551 27-Aug-09 09:34:00 169.9698029 6540.80859 81.2483597 0.27680099 27-Aug-09 09:35:00 170.5096741 6555.28125 81.2483597 0.2768265 27-Aug-09 09:36:00 170.2611237 6528.9292 81.6088715 0.27685198 27-Aug-09 09:37:00 171.2545471 6558.93311 81.8119736 0.27687746 27-Aug-09 09:38:00 170.4933319 6540.2959 82.0150833 0.27690294 27-Aug-09 09:39:00 170.4290771 6515.3623 82.1411438 0.27692842 27-Aug-09 09:40:00 170.7388763 6550.84668 81.8306046 0.27695391 27-Aug-09 09:41:00 169.9107513 6530.18164 81.6436081 0.27697939 27-Aug-09 09:42:00 169.2546844 6501.21387 82.2595825 0.27700487 27-Aug-09 09:43:00 168.7638855 6573.52539 82.5180435 0.27703035 27-Aug-09 09:44:00 169.3734894 6496.00146 82.7244949 0.27705583 27-Aug-09 09:45:00 169.9159088 6502.12793 82.930954 0.27708131 27-Aug-09 09:46:00 170.2431183 6527.24561 82.8035202 0.27710679 27-Aug-09 09:47:00 170.5703125 6548.19238 82.7095871 0.27713227 27-Aug-09 09:48:00 171.2966003 6526.34424 82.8139572 0.27715775 27-Aug-09 09:49:00 171.0566101 6536.81445 83.4094009 0.27718323 27-Aug-09 09:50:00 170.1865997 6526.56787 83.3426743 0.27720872 27-Aug-09 09:51:00 169.4387665 6492.854 83.2400131 0.2772342 27-Aug-09 09:52:00 169.2298431 6478.37012 83.137352 0.27725968 27-Aug-09 09:53:00 169.6777191 6485.60547 83.4042664 0.27728516 27-Aug-09 09:54:00 170.1964111 6555.73682 83.7533188 0.27731064 27-Aug-09 09:55:00 170.40979 6533.55273 83.3529358 0.27733612 27-Aug-09 09:56:00 169.8905182 6509.45264 83.2502747 0.2773616 27-Aug-09 09:57:00 169.8225555 6495.43896 83.1476135 0.27738708 27-Aug-09 09:58:00 170.2397461 6544.74561 83.4402008 0.27741256 27-Aug-09 09:59:00 169.8345642 6517.43408 83.5171967 0.27743804 27-Aug-09 10:00:00 170.5185089 6534.90625 83.9021759 0.27746353



### Page 2 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 10:01:00 171.1015778 6534.36377 84.1753387 0.27748901 27-Aug-09 10:02:00 169.8465881 6521.60742 84.3238297 0.27751449 27-Aug-09 10:03:00 168.8244629 6514.77539 84.1628342 0.27753997 27-Aug-09 10:04:00 168.8739929 6522.40234 84.3046799 0.27756545 27-Aug-09 10:05:00 169.1626129 6497.54102 84.2054138 0.27759093 27-Aug-09 10:06:00 169.3180084 6490.57422 84.1061401 0.27761641 27-Aug-09 10:07:00 169.373291 6493.58496 84.2460938 0.27764189 27-Aug-09 10:08:00 170.2609253 6526.21582 84.5043182 0.27766737 27-Aug-09 10:09:00 169.7085571 6516.54492 84.4005203 0.27769285 27-Aug-09 10:10:00 169.8931732 6522.59473 84.6025162 0.27771834 27-Aug-09 10:11:00 170.3612366 6530.39258 84.4497757 0.27774382 27-Aug-09 10:12:00 170.4580536 6545.97656 84.4452896 0.2777693 27-Aug-09 10:13:00 170.7708435 6557.22461 84.5992813 0.27779478 27-Aug-09 10:14:00 170.3340302 6544.11572 84.4106445 0.27782026 27-Aug-09 10:15:00 170.1284485 6519.50586 84.1546555 0.27784574 27-Aug-09 10:16:00 170.148056 6540.22656 84.3582458 0.27787122 27-Aug-09 10:17:00 170.7887573 6522.89111 84.5618286 0.2778967 27-Aug-09 10:18:00 170.7462769 6541.27441 84.8790359 0.27792218 27-Aug-09 10:19:00 169.2931976 6504.15381 84.5710526 0.27794766 27-Aug-09 10:20:00 169.6741791 6527.43799 84.532547 0.27797315 27-Aug-09 10:21:00 171.3950043 6544.5498 84.9945297 0.27799863 27-Aug-09 10:22:00 169.0497437 6482.29932 85.3425522 0.27802414 27-Aug-09 10:23:00 169.6987457 6518.78418 85.4446564 0.27804962 27-Aug-09 10:24:00 170.9640808 6552.09131 85.5467606 0.2780751 27-Aug-09 10:25:00 170.7471008 6540.90771 85.2739868 0.27810058 27-Aug-09 10:26:00 170.3076324 6528.15918 85.1187286 0.27812606 27-Aug-09 10:27:00 169.1798706 6493.50781 85.2178192 0.27815154 27-Aug-09 10:28:00 169.1698914 6464.56445 84.7558441 0.27817702 27-Aug-09 10:29:00 169.2706146 6515.53271 84.3708572 0.2782025 27-Aug-09 10:30:00 170.1027222 6561.27002 84.7748871 0.27822798 27-Aug-09 10:31:00 169.7344818 6535.26025 85.2921066 0.27825347 27-Aug-09 10:32:00 171.1630249 6533.01172 85.1368408 0.27827895 27-Aug-09 10:33:00 170.8136139 6567.79736 85.3016663 0.27830443 27-Aug-09 10:34:00 170.492569 6549.41406 85.1990051 0.27832991 27-Aug-09 10:35:00 170.6349182 6503.00293 85.096344 0.27835539 27-Aug-09 10:36:00 169.9285889 6480.76563 85.3102188 0.27838087 27-Aug-09 10:37:00 170.2747955 6512.79395 85.6233368 0.27840635 27-Aug-09 10:38:00 169.989624 6508.24854 85.7645035 0.27843183 27-Aug-09 10:39:00 170.2254944 6542.42334 86.2264786 0.27845731 27-Aug-09 10:40:00 170.913269 6541.68994 85.9521179 0.27848279



### Page 3 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 10:41:00 170.5401764 6544.84326 86.2495804 0.27850828 27-Aug-09 10:42:00 170.1917419 6556.65039 87.1263199 0.27853376 27-Aug-09 10:43:00 169.6205444 6525.42041 86.769722 0.27855924 27-Aug-09 10:44:00 169.0826111 6475.10059 86.3039246 0.27858472 27-Aug-09 10:45:00 169.0826111 6504.6792 86.1226349 0.2786102 27-Aug-09 10:46:00 169.2366943 6512.37939 85.6148758 0.27863568 27-Aug-09 10:47:00 169.5448456 6509.87402 85.1071167 0.27866116 27-Aug-09 10:48:00 170.2787781 6529.4917 84.9971008 0.27868664 27-Aug-09 10:49:00 170.4257202 6526.43604 84.5145874 0.27871212 27-Aug-09 10:50:00 169.9334259 6498.93457 84.7279663 0.2787376 27-Aug-09 10:51:00 169.4411316 6504.25146 85.1937714 0.27876309 27-Aug-09 10:52:00 169.5142822 6491.60107 85.0753784 0.27878857 27-Aug-09 10:53:00 169.2260437 6496.6123 85.1972885 0.27881405 27-Aug-09 10:54:00 169.6086121 6514.94629 85.0432968 0.27883953 27-Aug-09 10:55:00 169.9716187 6500.8291 85.2092133 0.27886501 27-Aug-09 10:56:00 170.3589935 6509.81299 84.8995743 0.27889049 27-Aug-09 10:57:00 170.3140259 6514.51855 84.6839828 0.27891597 27-Aug-09 10:58:00 169.7074738 6510.66846 84.9971008 0.27894145 27-Aug-09 10:59:00 170.3447266 6515.31299 85.053566 0.27896693 27-Aug-09 11:00:00 170.6869354 6529.49121 85.3996811 0.27899241 27-Aug-09 11:01:00 170.3101959 6528.75781 85.5530472 0.2790179 27-Aug-09 11:02:00 170.745697 6516.33643 85.7064133 0.27904338 27-Aug-09 11:03:00 169.3813629 6498.97119 85.8597794 0.27906886 27-Aug-09 11:04:00 168.2611389 6500.43799 86.2444458 0.27909434 27-Aug-09 11:05:00 168.9891205 6490.50098 86.4888763 0.27911982 27-Aug-09 11:06:00 169.685379 6490.25684 86.3361359 0.2791453 27-Aug-09 11:07:00 169.8771973 6473.14502 86.3380737 0.27917078 27-Aug-09 11:08:00 168.9958649 6511.27979 86.5422821 0.27919626 27-Aug-09 11:09:00 169.6953583 6533.31299 86.7464905 0.27922174 27-Aug-09 11:10:00 170.2044983 6523.14453 86.9327545 0.27924725 27-Aug-09 11:11:00 170.7136383 6517.04834 87.0880203 0.27927274 27-Aug-09 11:12:00 170.2698059 6510.30176 87.0811462 0.27929822 27-Aug-09 11:13:00 169.7931213 6500.36475 86.979332 0.2793237 27-Aug-09 11:14:00 168.8777466 6520.66064 87.2898636 0.27934918 27-Aug-09 11:15:00 170.7681427 6545.7417 87.3101501 0.27937466 27-Aug-09 11:16:00 170.4526978 6527.16895 86.9194565 0.27940014 27-Aug-09 11:17:00 170.1081848 6489.64551 87.0734482 0.27942562 27-Aug-09 11:18:00 170.1647491 6501.13477 87.2274399 0.2794511 27-Aug-09 11:19:00 170.2853394 6496.73486 87.3814316 0.27947658 27-Aug-09 11:20:00 169.1207428 6488.42334 87.1278458 0.27950206



### Page 4 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 11:21:00 169.4689484 6485.53369 86.8223572 0.27952754 27-Aug-09 11:22:00 169.6340485 6509.13232 86.655098 0.27955303 27-Aug-09 11:23:00 170.1660919 6532.73096 87.1786728 0.27957851 27-Aug-09 11:24:00 170.1214294 6535.69873 87.1016769 0.27960399 27-Aug-09 11:25:00 170.3387604 6516.90186 87.0246811 0.27962947 27-Aug-09 11:26:00 169.9885101 6513.11279 86.9476852 0.27965495 27-Aug-09 11:27:00 169.7198181 6490.37891 86.9168854 0.27968043 27-Aug-09 11:28:00 169.4511261 6491.73779 87.4918518 0.27970591 27-Aug-09 11:29:00 169.403656 6495.68994 87.2876434 0.27973139 27-Aug-09 11:30:00 170.1892548 6526.05078 87.0834351 0.27975687 27-Aug-09 11:31:00 170.4193115 6512.37402 86.8792267 0.27978235 27-Aug-09 11:32:00 169.0139465 6469.82031 87.1786728 0.27980784 27-Aug-09 11:33:00 168.1738129 6515.58203 87.0902405 0.27983332 27-Aug-09 11:34:00 168.9933167 6510.48535 86.9881363 0.2798588 27-Aug-09 11:35:00 170.2270508 6543.25342 86.8860321 0.27988428 27-Aug-09 11:36:00 170.7331696 6555.4707 87.1576309 0.27990976 27-Aug-09 11:37:00 170.5620575 6552.90381 86.6081543 0.27993524 27-Aug-09 11:38:00 170.2055969 6544.60498 86.8288574 0.27996072 27-Aug-09 11:39:00 169.60672 6498.33545 86.3060455 0.2799862 27-Aug-09 11:40:00 168.8327484 6496.28271 86.5052948 0.28001168 27-Aug-09 11:41:00 169.0710449 6521.31445 86.3069839 0.28003716 27-Aug-09 11:42:00 170.9378815 6568.24316 86.3163071 0.28006265 27-Aug-09 11:43:00 171.0399475 6565.15234 86.4869461 0.28008813 27-Aug-09 11:44:00 170.2267609 6557.37402 86.327858 0.28011361 27-Aug-09 11:45:00 170.1571198 6516.13867 86.4805679 0.28013909 27-Aug-09 11:46:00 169.5567474 6537.36279 86.1109848 0.28016457 27-Aug-09 11:47:00 169.7697296 6529.22217 86.1608658 0.28019005 27-Aug-09 11:48:00 170.4747162 6550.89355 86.4549026 0.28021553 27-Aug-09 11:49:00 170.5673218 6547.81152 86.3009109 0.28024101 27-Aug-09 11:50:00 169.6325378 6529.6748 86.5550613 0.28026649 27-Aug-09 11:51:00 170.00177 6542.1416 87.0132904 0.28029197 27-Aug-09 11:52:00 170.3709869 6556.96143 87.188942 0.28031746 27-Aug-09 11:53:00 170.8801422 6588.40479 87.188942 0.28034294 27-Aug-09 11:54:00 170.0361328 6523.38037 87.5379944 0.28036842 27-Aug-09 11:55:00 169.7425537 6520.59912 87.6443863 0.2803939 27-Aug-09 11:56:00 170.8079987 6550.42285 87.3338547 0.28041938 27-Aug-09 11:57:00 170.3863068 6559.77295 87.4225006 0.28044486 27-Aug-09 11:58:00 169.3957367 6510.58838 87.2685013 0.28047037 27-Aug-09 11:59:00 169.1375427 6505.22656 87.3428497 0.28049585 27-Aug-09 12:00:00 169.1375427 6503.84814 87.188942 0.28052133



### Page 5 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 12:01:00 170.2178955 6533.65918 87.5020599 0.28054681 27-Aug-09 12:02:00 170.9772186 6526.06934 87.23069 0.2805723 27-Aug-09 12:03:00 171.321106 6556.96191 87.1252975 0.28059778 27-Aug-09 12:04:00 170.3847809 6568.87891 86.9725571 0.28062326 27-Aug-09 12:05:00 171.1953735 6576.43066 86.9896851 0.28064874 27-Aug-09 12:06:00 169.7220001 6545.90039 87.3002167 0.28067422 27-Aug-09 12:07:00 169.6167908 6527.2915 87.1371841 0.2806997 27-Aug-09 12:08:00 168.9642029 6498.59863 86.9819183 0.28072518 27-Aug-09 12:09:00 169.3428497 6523.25879 87.0980377 0.28075066 27-Aug-09 12:10:00 169.896637 6524.73779 87.0400848 0.28077614 27-Aug-09 12:11:00 169.9685059 6524.16211 87.5213089 0.28080162 27-Aug-09 12:12:00 169.9321899 6508.65186 87.5983047 0.28082711 27-Aug-09 12:13:00 169.4923248 6525.15234 87.6753006 0.28085259 27-Aug-09 12:14:00 169.5792694 6541.65283 87.7522964 0.28087807 27-Aug-09 12:15:00 170.9722595 6556.35693 88.1098251 0.28090355 27-Aug-09 12:16:00 171.3225708 6553.34131 87.9866257 0.28092903 27-Aug-09 12:17:00 170.6003265 6533.95264 87.8634338 0.28095451 27-Aug-09 12:18:00 169.6727753 6495.6958 87.7402344 0.28097999 27-Aug-09 12:19:00 169.2330017 6540.06396 87.6170425 0.28100547 27-Aug-09 12:20:00 169.5571899 6533.74805 87.8074799 0.28103095 27-Aug-09 12:21:00 170.0888214 6546.68945 87.6534882 0.28105643 27-Aug-09 12:22:00 170.7587433 6562.00391 87.4917908 0.28108191 27-Aug-09 12:23:00 170.9809723 6592.38672 86.875824 0.2811074 27-Aug-09 12:24:00 170.8368835 6566.2041 87.3340454 0.28113288 27-Aug-09 12:25:00 170.085144 6538.62793 87.7922668 0.28115836 27-Aug-09 12:26:00 169.1201477 6499.48438 87.8151779 0.28118384 27-Aug-09 12:27:00 169.1070251 6502.67773 87.8151779 0.28120932 27-Aug-09 12:28:00 169.4218292 6516.79492 87.8151779 0.2812348 27-Aug-09 12:29:00 169.8513794 6529.52197 87.9135132 0.28126028 27-Aug-09 12:30:00 169.6997223 6529.68604 88.3793182 0.28128576 27-Aug-09 12:31:00 169.8138428 6557.73584 87.9075775 0.28131124 27-Aug-09 12:32:00 170.7141266 6564.29541 88.0748367 0.28133672 27-Aug-09 12:33:00 170.9615631 6547.79492 88.3803253 0.28136221 27-Aug-09 12:34:00 170.2323151 6532.25342 88.068779 0.28138769 27-Aug-09 12:35:00 170.3313751 6527.26172 87.6029816 0.28141317 27-Aug-09 12:36:00 169.6642151 6523.35547 87.3350601 0.28143865 27-Aug-09 12:37:00 169.8871002 6525.33545 87.3660355 0.28146413 27-Aug-09 12:38:00 169.0766144 6495.63477 87.597023 0.28148961 27-Aug-09 12:39:00 168.6212311 6498.31152 87.8280182 0.28151509 27-Aug-09 12:40:00 169.5686188 6525.0791 88.0590057 0.28154057



### Page 6 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 12:41:00 170.6591339 6548.3042 88.4414215 0.28156605 27-Aug-09 12:42:00 170.373703 6541.84863 88.077179 0.28159153 27-Aug-09 12:43:00 170.6183014 6559.59717 88.0004959 0.28161702 27-Aug-09 12:44:00 170.9653015 6573.70068 87.9238129 0.2816425 27-Aug-09 12:45:00 170.6999054 6555 87.8471298 0.28166798 27-Aug-09 12:46:00 169.7997589 6536.29932 88.1283035 0.28168392 27-Aug-09 12:47:00 169.5701141 6520.81787 87.8998795 0.28167754 27-Aug-09 12:48:00 169.3605804 6534.31006 88.0538712 0.28167117 27-Aug-09 12:49:00 169.734314 6547.80273 88.0966873 0.28166482 27-Aug-09 12:50:00 170.1080322 6558.45898 88.0354843 0.28165844 27-Aug-09 12:51:00 169.4612427 6540.08301 87.9742889 0.28165206 27-Aug-09 12:52:00 169.4440002 6545.44482 87.9130936 0.28164569 27-Aug-09 12:53:00 169.4484711 6550.10645 87.8518982 0.28163931 27-Aug-09 12:54:00 168.4985809 6548.46973 87.8767776 0.28163296 27-Aug-09 12:55:00 170.0142975 6548.95605 88.0307693 0.28162658 27-Aug-09 12:56:00 170.4215088 6571.59863 88.0153732 0.2816202 27-Aug-09 12:57:00 170.2444611 6573.0376 87.9212341 0.28161383 27-Aug-09 12:58:00 169.1786041 6506.5127 88.0787277 0.28160748 27-Aug-09 12:59:00 169.3507233 6537.55859 87.9221649 0.2816011 27-Aug-09 13:00:00 169.3125763 6532.11914 88.1591034 0.28159472 27-Aug-09 13:01:00 169.5561981 6543.2417 88.2617645 0.28158835 27-Aug-09 13:02:00 170.7547455 6567.07617 88.3644257 0.281582 27-Aug-09 13:03:00 170.8305054 6572.6377 88.1283035 0.28157562 27-Aug-09 13:04:00 170.5957184 6583.57666 88.1283035 0.28156924 27-Aug-09 13:05:00 169.9676971 6544.15869 88.1283035 0.28156286 27-Aug-09 13:06:00 170.5710602 6576.18213 87.9383698 0.28155649 27-Aug-09 13:07:00 170.2480316 6566.64844 88.3858719 0.28155014 27-Aug-09 13:08:00 169.5722198 6549.96436 88.1515961 0.28154376 27-Aug-09 13:09:00 169.616333 6521.19775 88.3068619 0.28153738 27-Aug-09 13:10:00 169.9675446 6580.8877 88.1648331 0.28153101 27-Aug-09 13:11:00 170.5402985 6552.93018 88.0969925 0.28152466 27-Aug-09 13:12:00 170.1680756 6559.61523 88.1155243 0.28151828 27-Aug-09 13:13:00 170.0981293 6566.30078 87.9621582 0.2815119 27-Aug-09 13:14:00 169.8063507 6560.17676 87.8087921 0.28150553 27-Aug-09 13:15:00 170.0473938 6524.02783 87.655426 0.28149918 27-Aug-09 13:16:00 170.2545319 6537.91064 87.5020599 0.2814928 27-Aug-09 13:17:00 169.7052002 6519.79248 88.112648 0.28148642 27-Aug-09 13:18:00 168.9416199 6506.52588 87.9144211 0.28148004 27-Aug-09 13:19:00 169.2804413 6509.19971 88.0170822 0.28147367 27-Aug-09 13:20:00 169.377243 6511.87402 88.119751 0.28146732



### Page 7 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 13:21:00 169.1670837 6513.17432 88.3683624 0.28146094 27-Aug-09 13:22:00 169.6386566 6517.84912 88.0299683 0.28145456 27-Aug-09 13:23:00 170.2182007 6530.59766 87.5641632 0.28144819 27-Aug-09 13:24:00 169.6958771 6484.50537 87.6431351 0.28144184 27-Aug-09 13:25:00 170.1439056 6514.37207 87.4366837 0.28143546 27-Aug-09 13:26:00 170.3150177 6544.23926 87.2302322 0.28142908 27-Aug-09 13:27:00 170.6189423 6559.71289 87.5020599 0.2814227 27-Aug-09 13:28:00 170.2001953 6527.89355 87.9537735 0.28141636 27-Aug-09 13:29:00 169.5707092 6505.31201 88.1283035 0.28140998 27-Aug-09 13:30:00 169.898056 6516.12891 88.0359039 0.2814036 27-Aug-09 13:31:00 170.121994 6523.80811 88.4414215 0.28139722 27-Aug-09 13:32:00 169.7880554 6522.73828 88.8880539 0.28139085 27-Aug-09 13:33:00 169.9006195 6531.05762 88.8061523 0.2813845 27-Aug-09 13:34:00 170.3186188 6531.28418 88.3101654 0.28137812 27-Aug-09 13:35:00 169.715271 6504.91992 88.2266388 0.28137174 27-Aug-09 13:36:00 169.0798187 6493.64209 88.3819046 0.28136536 27-Aug-09 13:37:00 169.2659454 6522.53027 88.0366592 0.28135902 27-Aug-09 13:38:00 170.1712341 6509.36084 87.8839111 0.28135264 27-Aug-09 13:39:00 170.1598053 6528.59912 88.1596146 0.28134626 27-Aug-09 13:40:00 170.5200348 6535.19922 88.3846436 0.28133988 27-Aug-09 13:41:00 171.5646667 6536.81494 88.2814178 0.28133354 27-Aug-09 13:42:00 170.3069153 6533.64746 88.1781921 0.28132716 27-Aug-09 13:43:00 170.5548859 6566.53809 88.197464 0.28132078 27-Aug-09 13:44:00 169.7204437 6541.48975 88.3313141 0.2813144 27-Aug-09 13:45:00 168.5708008 6505.20508 88.4651718 0.28130803 27-Aug-09 13:46:00 169.210495 6500.76221 88.5990219 0.28130168 27-Aug-09 13:47:00 170.7658844 6540.80469 88.7328796 0.2812953 27-Aug-09 13:48:00 170.79245 6567.6001 88.8154221 0.28128892 27-Aug-09 13:49:00 170.921524 6547.32422 88.4414215 0.28128254 27-Aug-09 13:50:00 171.1286469 6544.95898 88.1552505 0.2812762 27-Aug-09 13:51:00 170.7000885 6549.19434 88.2322464 0.28126982 27-Aug-09 13:52:00 169.063858 6527.71924 88.3092422 0.28126344 27-Aug-09 13:53:00 169.2663269 6513.85596 88.3862381 0.28125706 27-Aug-09 13:54:00 169.3860168 6511.88965 88.4121704 0.28125072 27-Aug-09 13:55:00 169.7327423 6509.92285 88.3089447 0.28124434 27-Aug-09 13:56:00 170.5871277 6537.76611 88.205719 0.28123796 27-Aug-09 13:57:00 170.614151 6542.92383 87.9666901 0.28123158 27-Aug-09 13:58:00 171.0965271 6547.71533 88.4190521 0.2812252 27-Aug-09 13:59:00 170.1565094 6536.33887 88.3158264 0.28121886 27-Aug-09 14:00:00 169.3514252 6507.97461 88.2126007 0.28121248



### Page 8 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 14:01:00 169.4527283 6513.6084 88.4414215 0.2812061 27-Aug-09 14:02:00 168.9928589 6508.71875 88.1490021 0.28119972 27-Aug-09 14:03:00 169.1873169 6534.34961 88.3042679 0.28119338 27-Aug-09 14:04:00 170.1629639 6556.13672 88.4057846 0.281187 27-Aug-09 14:05:00 170.4044189 6539.58008 88.100296 0.28118062 27-Aug-09 14:06:00 170.2409821 6539.10107 87.8357086 0.28117424 27-Aug-09 14:07:00 170.3715973 6523.38428 88.1180954 0.28116786 27-Aug-09 14:08:00 169.5587006 6514.61621 87.9138794 0.28116152 27-Aug-09 14:09:00 169.2099762 6499.7168 87.709671 0.28115514 27-Aug-09 14:10:00 169.9111633 6570.82275 87.5054626 0.28114876 27-Aug-09 14:11:00 170.4022369 6564.03271 87.8049088 0.28114238 27-Aug-09 14:12:00 170.3559875 6553.74463 87.5174561 0.28113604 27-Aug-09 14:13:00 170.6431885 6550.89355 87.7995224 0.28112966 27-Aug-09 14:14:00 170.1712036 6532.30273 87.5020599 0.28112328 27-Aug-09 14:15:00 170.0391541 6533.99707 87.5020599 0.2811169 27-Aug-09 14:16:00 170.1460114 6522.53467 87.5467911 0.28111055 27-Aug-09 14:17:00 169.8871002 6522.1333 87.7638474 0.28110418 27-Aug-09 14:18:00 170.8066559 6545.60107 87.554245 0.2810978 27-Aug-09 14:19:00 170.56604 6555.70654 87.5636597 0.28109142 27-Aug-09 14:20:00 170.5717621 6536.97852 87.2556686 0.28108504 27-Aug-09 14:21:00 169.7053375 6521.77881 87.4301987 0.2810787 27-Aug-09 14:22:00 169.0015564 6521.65771 88.0193939 0.28107232 27-Aug-09 14:23:00 169.355011 6540.125 88.0914688 0.28106594 27-Aug-09 14:24:00 169.7084503 6560.18896 88.0300674 0.28105956 27-Aug-09 14:25:00 169.9757233 6530.85986 87.9686737 0.28105322 27-Aug-09 14:26:00 170.2415314 6529.13281 87.9072723 0.28104684 27-Aug-09 14:27:00 169.3237 6499.87012 87.8458786 0.28104046 27-Aug-09 14:28:00 170.6329041 6520.31494 87.931076 0.28103408 27-Aug-09 14:29:00 170.6092987 6528.93213 88.1628799 0.28102773 27-Aug-09 14:30:00 170.0906219 6532.93604 88.3946838 0.28102136 27-Aug-09 14:31:00 170.4086914 6516.38965 88.6264877 0.28101498 27-Aug-09 14:32:00 169.8900757 6505.02441 88.8582916 0.2810086 27-Aug-09 14:33:00 170.1629639 6519.56055 89.0900955 0.28100222 27-Aug-09 14:34:00 170.1530609 6538.09619 89.3218994 0.28099588 27-Aug-09 14:35:00 170.7651367 6542.53271 89.4416656 0.2809895 27-Aug-09 14:36:00 170.3517303 6513.52832 88.9899445 0.28098312 27-Aug-09 14:37:00 169.7666779 6525.26221 88.4414215 0.28097674 27-Aug-09 14:38:00 169.8653259 6524.35986 88.9009781 0.28097039 27-Aug-09 14:39:00 170.1174927 6536.10352 89.1063004 0.28096402 27-Aug-09 14:40:00 170.1582336 6532.93213 89.3116226 0.28095764



### Page 9 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 14:41:00 169.1375427 6524.49854 89.2158051 0.28095126 27-Aug-09 14:42:00 169.0284271 6510.02686 88.4056854 0.28094491 27-Aug-09 14:43:00 169.8744965 6507.02588 88.3035812 0.28093854 27-Aug-09 14:44:00 170.7363129 6539.5249 88.2014771 0.28093216 27-Aug-09 14:45:00 170.7369843 6534.54102 88.0993729 0.28092578 27-Aug-09 14:46:00 170.2371826 6529.55762 87.9972687 0.2809194 27-Aug-09 14:47:00 170.5987549 6530.68896 87.8951569 0.28091305 27-Aug-09 14:48:00 170.5061951 6536.73926 87.8819122 0.28090668 27-Aug-09 14:49:00 170.4136505 6526.67578 88.1898956 0.2809003 27-Aug-09 14:50:00 170.5191498 6522.14551 88.3840179 0.28089392 27-Aug-09 14:51:00 170.2019958 6504.90576 88.3900909 0.28088757 27-Aug-09 14:52:00 169.3824921 6513.6875 88.0820999 0.2808812 27-Aug-09 14:53:00 170.2154999 6533.23584 87.8973083 0.28087482 27-Aug-09 14:54:00 170.9555969 6526.17725 88.4414215 0.28086844 27-Aug-09 14:55:00 170.5743866 6519.11914 88.4977417 0.28086209 27-Aug-09 14:56:00 170.2612457 6512.06055 89.1387329 0.28085572 27-Aug-09 14:57:00 169.3123932 6499.93701 89.2914734 0.28084934 27-Aug-09 14:58:00 169.4373169 6494.32666 89.4334641 0.28084296 27-Aug-09 14:59:00 170.6268463 6526.68652 88.9415436 0.28083658 27-Aug-09 15:00:00 170.2242126 6522.62207 88.4496231 0.28083023 27-Aug-09 15:01:00 170.0591125 6503.07813 88.6222916 0.28082386 27-Aug-09 15:02:00 169.8940125 6507.63135 88.8062286 0.28081748 27-Aug-09 15:03:00 170.0867767 6549.86816 88.9087524 0.2808111 27-Aug-09 15:04:00 170.628067 6570.37646 89.4006729 0.28080475 27-Aug-09 15:05:00 169.196167 6497.95264 89.1994095 0.28079838 27-Aug-09 15:06:00 168.4592743 6476.16406 89.1285477 0.280792 27-Aug-09 15:07:00 169.624588 6527.13037 89.1285477 0.28078562 27-Aug-09 15:08:00 170.5770721 6546.87842 89.6347275 0.28077927 27-Aug-09 15:09:00 170.6736145 6523.4292 89.4968948 0.28077289 27-Aug-09 15:10:00 170.0319366 6527.8291 89.1917572 0.28076652 27-Aug-09 15:11:00 170.0206909 6524.07666 88.8866196 0.28076014 27-Aug-09 15:12:00 170.4295349 6517.63525 88.4414215 0.28075376 27-Aug-09 15:13:00 169.4772034 6517.63525 88.4808502 0.28074741 27-Aug-09 15:14:00 170.884491 6523.48389 88.9727707 0.28074104 27-Aug-09 15:15:00 170.2917633 6519.45654 88.9180832 0.28073466 27-Aug-09 15:16:00 168.9645081 6508.29102 89.1785965 0.28072828 27-Aug-09 15:17:00 169.5514679 6507.92432 89.2555923 0.28072193 27-Aug-09 15:18:00 169.1173096 6497.10107 89.3325882 0.28071555 27-Aug-09 15:19:00 169.72995 6506.47021 89.409584 0.28070918 27-Aug-09 15:20:00 170.3603363 6520.12891 89.1285477 0.2807028



### Page 10 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 15:21:00 169.6525421 6495.79346 88.5874329 0.28069645 27-Aug-09 15:22:00 170.0278778 6504.66699 88.1283035 0.28069007 27-Aug-09 15:23:00 170.1638489 6540.04004 87.7102432 0.2806837 27-Aug-09 15:24:00 171.1084442 6527.35254 87.5071411 0.28067732 27-Aug-09 15:25:00 169.2849579 6512.34424 87.3040314 0.28067094 27-Aug-09 15:26:00 170.7983093 6525.22852 87.3875046 0.28066459 27-Aug-09 15:27:00 169.1186218 6538.11279 87.8457336 0.28065822 27-Aug-09 15:28:00 169.9849396 6556.64404 88.1873322 0.28065184 27-Aug-09 15:29:00 171.3356323 6545.41162 88.3413239 0.28064546 27-Aug-09 15:30:00 170.189682 6519.48096 88.2258301 0.28063911 27-Aug-09 15:31:00 169.873291 6537.71094 88.0291443 0.28063273 27-Aug-09 15:32:00 169.7135925 6525.52197 87.9897079 0.28062636 27-Aug-09 15:33:00 169.6114655 6498.01807 87.5277252 0.28061998 27-Aug-09 15:34:00 169.2197266 6494.32422 87.2598495 0.2806136 27-Aug-09 15:35:00 169.2816315 6482.33008 87.5257645 0.28060725 27-Aug-09 15:36:00 169.8203735 6492.62793 87.7916718 0.28060088 27-Aug-09 15:37:00 170.100708 6519.02881 88.057579 0.2805945 27-Aug-09 15:38:00 170.4094849 6528.55908 88.3234863 0.28058812 27-Aug-09 15:39:00 170.125824 6520.05469 88.5894012 0.28058177 27-Aug-09 15:40:00 170.3349762 6534.01611 88.9078217 0.28057539 27-Aug-09 15:41:00 170.7105255 6553.36816 89.4416656 0.28056902 27-Aug-09 15:42:00 170.4193268 6541.35352 89.3765411 0.28056264 27-Aug-09 15:43:00 170.2183075 6540.83984 88.7252884 0.28055629 27-Aug-09 15:44:00 169.89711 6535.5293 88.4310684 0.28054991 27-Aug-09 15:45:00 169.5759125 6502.45215 88.2758026 0.28054354 27-Aug-09 15:46:00 169.7078857 6510.68066 88.1751862 0.28053716 27-Aug-09 15:47:00 170.5506287 6540.46729 89.112915 0.28053078 27-Aug-09 15:48:00 170.6042175 6539.5874 89.2812271 0.28052443 27-Aug-09 15:49:00 170.6043854 6529.02686 89.4364929 0.28051805 27-Aug-09 15:50:00 170.5053253 6521.18018 89.2748413 0.28051168 27-Aug-09 15:51:00 170.3763275 6518.7417 89.428833 0.2805053 27-Aug-09 15:52:00 170.1827087 6540.62939 89.1593475 0.28049895 27-Aug-09 15:53:00 170.4589081 6574.54736 89.3595352 0.28049257 27-Aug-09 15:54:00 170.4597015 6562.65137 89.4416656 0.2804862 27-Aug-09 15:55:00 169.786377 6526.24023 89.6534576 0.28047982 27-Aug-09 15:56:00 169.417572 6515.97314 89.5664291 0.28047347 27-Aug-09 15:57:00 170.033905 6524.66943 89.7161407 0.28046709 27-Aug-09 15:58:00 170.5429993 6532.31055 88.6709824 0.28046072 27-Aug-09 15:59:00 170.4200745 6517.15479 88.2013626 0.28045434 27-Aug-09 16:00:00 169.8708801 6501.99854 88.061142 0.28044796



### Page 11 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 16:01:00 169.9496918 6497.00342 88.3890915 0.28044161 27-Aug-09 16:02:00 169.0352173 6516.59521 88.717041 0.28043523 27-Aug-09 16:03:00 170.3656311 6523.20996 88.5671082 0.28042886 27-Aug-09 16:04:00 170.5749664 6530.15137 88.7510452 0.28042248 27-Aug-09 16:05:00 170.5836639 6540.55908 88.4982681 0.28041613 27-Aug-09 16:06:00 171.0915222 6529.00244 88.0103455 0.28040975 27-Aug-09 16:07:00 170.7725525 6529.00244 87.7539139 0.28040338 27-Aug-09 16:08:00 171.3074188 6526.69873 87.6518097 0.280397 27-Aug-09 16:09:00 170.2491608 6509.17139 87.5497055 0.28039065 27-Aug-09 16:10:00 169.9544067 6517.87988 87.5841904 0.28038427 27-Aug-09 16:11:00 171.2598114 6537.49121 87.7381821 0.28037789 27-Aug-09 16:12:00 170.7011871 6537.90088 88.1231689 0.28037152 27-Aug-09 16:13:00 170.1923828 6554.03467 87.8408508 0.28036514 27-Aug-09 16:14:00 169.7826385 6534.01416 87.8620224 0.28035879 27-Aug-09 16:15:00 170.0083618 6512.91748 88.6619339 0.28035241 27-Aug-09 16:16:00 170.3611908 6518.51563 89.0649033 0.28034604 27-Aug-09 16:17:00 169.5339813 6509.71533 88.9121628 0.28033966 27-Aug-09 16:18:00 169.7074127 6491.69922 88.4546814 0.28033331 27-Aug-09 16:19:00 169.6708527 6493.95996 87.8151779 0.28032693 27-Aug-09 16:20:00 170.1742249 6519.38916 87.7553635 0.28032055 27-Aug-09 16:21:00 170.52948 6525.40918 88.555275 0.28031418 27-Aug-09 16:22:00 169.8370361 6509.6665 89.0852737 0.28030783 27-Aug-09 16:23:00 169.1825867 6501.11621 88.9325256 0.28030145 27-Aug-09 16:24:00 169.1050568 6496.20313 88.8884811 0.28029507 27-Aug-09 16:25:00 169.5057983 6500.30664 89.374939 0.2802887 27-Aug-09 16:26:00 170.3030396 6533.49121 89.1688232 0.28028232 27-Aug-09 16:27:00 171.0404053 6539.1167 89.3701935 0.28027597 27-Aug-09 16:28:00 170.4250336 6522.19434 89.5715637 0.28026959 27-Aug-09 16:29:00 170.0727539 6512.66064 89.6637497 0.28026322 27-Aug-09 16:30:00 170.13974 6515.97607 89.4103546 0.28025684 27-Aug-09 16:31:00 170.545929 6533.02686 89.4416656 0.28025049 27-Aug-09 16:32:00 171.2694397 6557.07813 89.4416656 0.28024411 27-Aug-09 16:33:00 170.8819885 6509.84814 89.7440948 0.28023773 27-Aug-09 16:34:00 170.1547241 6487.95264 89.6844025 0.28023136 27-Aug-09 16:35:00 169.9307251 6514.37207 89.6247177 0.28022501 27-Aug-09 16:36:00 169.5973511 6496.97314 89.5650253 0.28021863 27-Aug-09 16:37:00 169.7999725 6495.23145 89.5053329 0.28021225 27-Aug-09 16:38:00 170.0408936 6497.77686 89.4456482 0.28020588 27-Aug-09 16:39:00 170.1095276 6519.59131 89.716629 0.2801995 27-Aug-09 16:40:00 170.2215118 6522.31543 89.3341522 0.28019315



### Page 12 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 16:41:00 170.70961 6550.08643 88.8764496 0.28018677 27-Aug-09 16:42:00 169.9752045 6499.86963 87.9627533 0.28018039 27-Aug-09 16:43:00 169.4077759 6517.25049 88.3387604 0.28017402 27-Aug-09 16:44:00 170.1007538 6521.41211 88.4414215 0.28016767 27-Aug-09 16:45:00 169.3354645 6498.00293 88.0672073 0.28016129 27-Aug-09 16:46:00 169.9875183 6534.9917 87.6089783 0.28015491 27-Aug-09 16:47:00 170.4713593 6532.21045 87.4430313 0.28014854 27-Aug-09 16:48:00 170.555954 6518.89844 87.3660355 0.28014219 27-Aug-09 16:49:00 170.057373 6528.12256 87.2890396 0.28013581 27-Aug-09 16:50:00 169.5587921 6522.15479 87.2120438 0.28012943 27-Aug-09 16:51:00 169.2341156 6512.8042 87.0914154 0.28012305 27-Aug-09 16:52:00 170.3270264 6519.6792 86.7757263 0.28011668 27-Aug-09 16:53:00 169.389328 6473.02246 86.621727 0.28011033 27-Aug-09 16:54:00 169.1146545 6463.67236 86.7526245 0.28010395 27-Aug-09 16:55:00 169.439682 6485.42871 87.0691681 0.28009757 27-Aug-09 16:56:00 169.8719482 6485.48975 86.8638458 0.2800912 27-Aug-09 16:57:00 169.4355927 6480.35596 86.6585159 0.28008485 27-Aug-09 16:58:00 168.9845123 6460.23438 86.6728058 0.28007847 27-Aug-09 16:59:00 170.2840118 6504.89795 86.8792648 0.28007209 27-Aug-09 17:00:00 169.7063904 6497.83496 87.0857162 0.28006572 27-Aug-09 17:01:00 170.5477905 6522.03564 87.2653122 0.28005934 27-Aug-09 17:02:00 170.6016846 6525.39697 87.4180527 0.28005299 27-Aug-09 17:03:00 170.5386505 6537.39893 87.3634644 0.28004661 27-Aug-09 17:04:00 169.7898712 6507.64404 87.322403 0.28004023 27-Aug-09 17:05:00 169.0138702 6470.00635 87.3737335 0.28003386 27-Aug-09 17:06:00 170.1628265 6490.31787 87.5631561 0.28002751 27-Aug-09 17:07:00 170.9913177 6522.21875 87.7158966 0.28002113 27-Aug-09 17:08:00 170.6863556 6523.56348 87.7055893 0.28001475 27-Aug-09 17:09:00 170.6522064 6518.79639 87.7141724 0.28000838 27-Aug-09 17:10:00 170.5758667 6533.22852 87.6899338 0.28000203 27-Aug-09 17:11:00 169.8788452 6495.50244 88.0939331 0.27999565 27-Aug-09 17:12:00 170.4197845 6502.23486 88.8154221 0.27998927 27-Aug-09 17:13:00 170.1124573 6543.36426 88.9694138 0.27998289 27-Aug-09 17:14:00 169.6847839 6511.27979 89.0607071 0.27997652 27-Aug-09 17:15:00 169.932663 6517.39111 89.2500305 0.27997017 27-Aug-09 17:16:00 170.7321014 6517.58301 89.6911926 0.27996379 27-Aug-09 17:17:00 170.0616455 6514.43994 89.4796524 0.27995741 27-Aug-09 17:18:00 169.903717 6522.854 89.7075653 0.27995104 27-Aug-09 17:19:00 170.4977112 6533.30762 89.9354858 0.27994469 27-Aug-09 17:20:00 170.8037109 6543.76074 90.1633987 0.27993831



### Page 13 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 17:21:00 170.3385773 6535.57227 90.3341827 0.27993193 27-Aug-09 17:22:00 169.9609528 6523.65527 89.8764801 0.27992555 27-Aug-09 17:23:00 170.2735748 6520.75195 89.4338989 0.27991921 27-Aug-09 17:24:00 170.5862122 6535.79541 89.2786407 0.27991283 27-Aug-09 17:25:00 170.8988342 6536.04248 89.4252701 0.27990645 27-Aug-09 17:26:00 170.7798462 6544.64111 88.4414215 0.27990007 27-Aug-09 17:27:00 170.0769043 6472.41797 88.6253586 0.2798937 27-Aug-09 17:28:00 169.2508698 6483.87012 88.809288 0.27988735 27-Aug-09 17:29:00 168.450882 6485.39844 89.4211349 0.27988097 27-Aug-09 17:30:00 169.632843 6485.03174 89.2510681 0.27987459 27-Aug-09 17:31:00 170.6422119 6508.47461 89.0468597 0.27986822 27-Aug-09 17:32:00 169.7098389 6504.76514 88.8426514 0.27986187 27-Aug-09 17:33:00 170.1916962 6497.79834 89.3492661 0.27985549 27-Aug-09 17:34:00 169.9037323 6522.94336 89.4416656 0.27984911 27-Aug-09 17:35:00 169.756073 6479.28711 89.4416656 0.27984273 27-Aug-09 17:36:00 170.1432953 6493.81152 89.4416656 0.27983639 27-Aug-09 17:37:00 170.235611 6514.22314 89.7460861 0.27983001 27-Aug-09 17:38:00 170.9166718 6534.63477 89.742363 0.27982363 27-Aug-09 17:39:00 169.8521423 6501.04297 90.1523972 0.27981725 27-Aug-09 17:40:00 170.1313019 6540.4834 90.562439 0.27981088 27-Aug-09 17:41:00 170.4380951 6528.96582 90.1583557 0.27980453 27-Aug-09 17:42:00 171.0272827 6529.18262 90.2704926 0.27979815 27-Aug-09 17:43:00 169.6585693 6511.21826 90.1177521 0.27979177 27-Aug-09 17:44:00 169.6086426 6515.28271 89.6846313 0.27978539 27-Aug-09 17:45:00 169.5587006 6480.84521 89.6213226 0.27977905 27-Aug-09 17:46:00 170.3649902 6517.98389 89.5714188 0.27977267 27-Aug-09 17:47:00 169.4240265 6476.56104 89.6086044 0.27976629 27-Aug-09 17:48:00 169.256424 6476.53076 89.5889664 0.27975991 27-Aug-09 17:49:00 169.1483459 6474.87158 89.5938721 0.27975357 27-Aug-09 17:50:00 169.7454224 6472.12109 89.1389847 0.27974719 27-Aug-09 17:51:00 169.3066101 6455.60547 89.0234146 0.27974081 27-Aug-09 17:52:00 169.3307037 6468.79785 88.7981262 0.27973443 27-Aug-09 17:53:00 170.2735901 6486.15381 88.5728378 0.27972806 27-Aug-09 17:54:00 170.3205109 6503.51025 88.8154221 0.27972171 27-Aug-09 17:55:00 170.1434479 6478.32715 89.2466049 0.27971533 27-Aug-09 17:56:00 169.8883057 6483.31738 89.3856583 0.27970895 27-Aug-09 17:57:00 170.1631927 6493.03418 89.2329178 0.27970257 27-Aug-09 17:58:00 170.6053314 6519.43213 89.2007217 0.27969623 27-Aug-09 17:59:00 170.1295929 6498.55615 89.4286346 0.27968985 27-Aug-09 18:00:00 169.6930389 6496.21631 89.6565552 0.27968347



### Page 14 of 15

### Plant Information Database Query

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 27-Aug-09 18:01:00 170.1477051 6510.9751 89.8844681 0.27967709 27-Aug-09 18:02:00 170.2306671 6500.68115 89.8456116 0.27967075 27-Aug-09 18:03:00 170.2426605 6498.64111 89.1285477 0.27966437 27-Aug-09 18:04:00 170.2968445 6522.45996 89.1285477 0.27965799 27-Aug-09 18:05:00 170.6030273 6549.00635 89.1285477 0.27965161 27-Aug-09 18:06:00 170.4259186 6519.38965 89.0271683 0.27964523 27-Aug-09 18:07:00 169.9036102 6469.72266 88.4495926 0.27963889 27-Aug-09 18:08:00 170.6526337 6448.18604 88.51091 0.27963251 27-Aug-09 18:09:00 170.8215637 6540.79102 88.5722198 0.27962613 27-Aug-09 18:10:00 169.7270508 6495.13965 88.6335297 0.27961975 27-Aug-09 18:11:00 169.5645599 6484.90918 88.6948395 0.27961341 27-Aug-09 18:12:00 170.2315674 6478.12451 88.7561569 0.27960703 27-Aug-09 18:13:00 169.9719086 6485.58789 89.1285477 0.27960065 27-Aug-09 18:14:00 169.9351501 6498.28711 89.0162125 0.27959427 27-Aug-09 18:15:00 170.5043793 6486.56543 88.9038773 0.27958792 27-Aug-09 18:16:00 170.6784821 6520.10449 88.7915344 0.27958155 27-Aug-09 18:17:00 170.8525848 6517.58594 88.6791992 0.27957517 27-Aug-09 18:18:00 170.2444763 6503.67139 88.566864 0.27956879 27-Aug-09 18:19:00 169.6322479 6494.08252 88.4545288 0.27956241 27-Aug-09 18:20:00 169.1784515 6493.64258 88.7663727 0.27955607 27-Aug-09 18:21:00 169.9720459 6524.60254 88.2391281 0.27954969 27-Aug-09 18:22:00 170.3070068 6508.68848 88.0427475 0.27954331 27-Aug-09 18:23:00 170.4831085 6498.72656 87.9400864 0.27953693 27-Aug-09 18:24:00 170.1592102 6512.29395 87.8374252 0.27953058 27-Aug-09 18:25:00 170.3404083 6512.15967 87.6560516 0.27952421 27-Aug-09 18:26:00 170.0316925 6504.09277 87.444313 0.27951783 27-Aug-09 18:27:00 169.7476654 6471.6416 87.3673172 0.27951145 27-Aug-09 18:28:00 169.8645325 6463.85596 87.2903214 0.27950507 27-Aug-09 18:29:00 169.2492065 6489.90234 87.2133255 0.27949873 27-Aug-09 18:30:00 170.0969238 6495.59814 87.3993988 0.27949235 27-Aug-09 18:31:00 170.2050018 6485.69775 87.7073822 0.27948597 27-Aug-09 18:32:00 170.2743378 6459.30859 87.6939697 0.27947959 27-Aug-09 18:33:00 169.2555237 6489.79248 87.7224045 0.27947325 27-Aug-09 18:34:00 170.2921906 6517.19434 87.5677795 0.27946687 27-Aug-09 18:35:00 170.0969238 6491.40869 87.413147 0.27946049



### Page 15 of 15Plant Information Source: polk-1pisrv Start Time: 09/01/2009 10:32

End Time: 09/01/2009 12:58 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 170.0567026 6587.21 79.881857 1.92634145 01-Sep-09 10:32:00 170.4930267 6569.86621 81.3327103 1.93360674 01-Sep-09 10:33:00 169.8574371 6579.58301 81.4093933 1.93355441 01-Sep-09 10:34:00 170.2223663 6589.71289 81.4860764 1.9335022 01-Sep-09 10:35:00 170.0543823 6622.64014 81.5571976 1.93344986 01-Sep-09 10:36:00 170.34758 6566.12549 81.3005447 1.93339765 01-Sep-09 10:37:00 170.6755981 6593.44336 81.0438919 1.93334532 01-Sep-09 10:38:00 170.9232483 6620.12256 80.7872314 1.9332931 01-Sep-09 10:39:00 170.7553711 6609.12207 80.5305786 1.93324077 01-Sep-09 10:40:00 170.6428986 6598.12158 80.2739258 1.93318856 01-Sep-09 10:41:00 170.5675812 6587.5249 80.0172653 1.93313622 01-Sep-09 10:42:00 170.2844849 6600.08301 80.2409821 1.93308401 01-Sep-09 10:43:00 169.9258423 6575.0542 80.1639862 1.93303168 01-Sep-09 10:44:00 170.3450317 6566.0708 80.0869904 1.93297946 01-Sep-09 10:45:00 169.5058746 6558.21484 80.0099945 1.93292713 01-Sep-09 10:46:00 169.7790375 6615.34619 80.1206207 1.93287492 01-Sep-09 10:47:00 169.9780273 6582.77002 80.2733612 1.93282259 01-Sep-09 10:48:00 169.6552277 6578.1377 80.1899643 1.93277037 01-Sep-09 10:49:00 169.7209167 6556.85791 80.0346985 1.93189442 01-Sep-09 10:50:00 169.7866058 6577.4165 79.8012543 1.92959595 01-Sep-09 10:51:00 169.830368 6557.27979 79.9509659 1.92729747 01-Sep-09 10:52:00 170.6894989 6603.13916 80.0934067 1.924999 01-Sep-09 10:53:00 170.883606 6606.84424 80.2054901 1.92360139 01-Sep-09 10:54:00 170.2178955 6591.64355 80.0502243 1.92365313 01-Sep-09 10:55:00 169.4880066 6589.34619 79.8810959 1.92370486 01-Sep-09 10:56:00 169.3265076 6574.07959 79.9346619 1.9237566 01-Sep-09 10:57:00 169.515625 6576.41455 79.8353958 1.92380822 01-Sep-09 10:58:00 170.1027222 6646.22998 79.7361298 1.92385995 01-Sep-09 10:59:00 170.5006714 6600.32178 79.7731323 1.92391169 01-Sep-09 11:00:00 170.4556427 6589.32129 79.9216309 1.92396343 01-Sep-09 11:01:00 171.0151825 6582.27295 79.6921692 1.92401516 01-Sep-09 11:02:00 170.3067474 6597.61768 79.3414307 1.92406678 01-Sep-09 11:03:00 170.1564636 6600.90771 79.2650528 1.92411852 01-Sep-09 11:04:00 169.1421204 6556.65039 79.1886826 1.92417026 01-Sep-09 11:05:00 169.6530609 6582.42773 79.1123123 1.92422199



### Page 1 of 4Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 01-Sep-09 11:06:00 170.0839691 6591.52148 79.305275 1.92427373 01-Sep-09 11:07:00 169.5222321 6582.86768 79.3783417 1.92432535 01-Sep-09 11:08:00 169.3961639 6617.79395 79.3783417 1.92437708 01-Sep-09 11:09:00 169.4734955 6594.14209 79.1340332 1.92442882 01-Sep-09 11:10:00 170.3675537 6600.61279 79.3404846 1.92448056 01-Sep-09 11:11:00 170.6805115 6603.25537 79.5469437 1.92453229 01-Sep-09 11:12:00 170.5108032 6591.2876 79.349411 1.92458391 01-Sep-09 11:13:00 170.4048309 6601.98389 79.2473068 1.92463565 01-Sep-09 11:14:00 170.9259338 6612.68066 79.1452026 1.92468739 01-Sep-09 11:15:00 170.9030914 6619.53516 79.0985794 1.92473912 01-Sep-09 11:16:00 170.2355957 6607.55371 79.2525787 1.92479086 01-Sep-09 11:17:00 170.3123169 6610.24268 79.7166214 1.92484248 01-Sep-09 11:18:00 170.4834137 6612.93164 79.867569 1.92489421 01-Sep-09 11:19:00 170.0961761 6610.05078 79.7002258 1.92494595 01-Sep-09 11:20:00 169.6735229 6579.32275 79.7753983 1.92499769 01-Sep-09 11:21:00 169.5558014 6557.45459 79.850563 1.9250493 01-Sep-09 11:22:00 169.4486084 6578.42627 79.9257278 1.92510104 01-Sep-09 11:23:00 169.7451172 6565.92725 79.7064285 1.92515278 01-Sep-09 11:24:00 169.6041718 6569.72266 80.3037796 1.92520452 01-Sep-09 11:25:00 169.5735626 6566.47705 80.3089981 1.92525625 01-Sep-09 11:26:00 169.9797058 6602.96191 79.7015839 1.92530787 01-Sep-09 11:27:00 170.0474854 6582.92285 79.6411209 1.92535961 01-Sep-09 11:28:00 169.6371613 6578.15576 79.5899277 1.92541134 01-Sep-09 11:29:00 169.1286926 6575.29639 79.5387421 1.92546308 01-Sep-09 11:30:00 169.9624329 6583.24658 79.4875488 1.92551482 01-Sep-09 11:31:00 169.871933 6595.37158 79.4363556 1.92556643 01-Sep-09 11:32:00 170.3100586 6618.7168 79.38517 1.92561817 01-Sep-09 11:33:00 170.5526733 6589.28223 79.7717896 1.92566991 01-Sep-09 11:34:00 169.3236237 6551.46143 80.225769 1.92572165 01-Sep-09 11:35:00 168.8619537 6583.83936 80.246376 1.92577338 01-Sep-09 11:36:00 170.1834106 6567.31104 80.169693 1.925825 01-Sep-09 11:37:00 171.0328827 6588.02881 80.0930099 1.92587674 01-Sep-09 11:38:00 170.6495667 6606.46387 80.0163269 1.92592847 01-Sep-09 11:39:00 170.0712585 6604.4834 79.6174774 1.92598021 01-Sep-09 11:40:00 170.2629242 6568.86084 79.5142517 1.92603195 01-Sep-09 11:41:00 170.1284485 6580.42969 79.411026 1.92608356 01-Sep-09 11:42:00 169.6867371 6582.73047 79.270546 1.9261353 01-Sep-09 11:43:00 170.3431244 6600.44385 79.1781464 1.92618704 01-Sep-09 11:44:00 169.7070313 6580.64307 79.3783417 1.92623878 01-Sep-09 11:45:00 169.5079041 6579.2373 79.3783417 1.92629051



### Page 2 of 4Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 01-Sep-09 11:46:00 169.8045502 6595.12695 79.6315765 1.92634213 01-Sep-09 11:47:00 169.75914 6571.36279 79.5289154 1.92639387 01-Sep-09 11:48:00 169.7769623 6604.96045 79.4262466 1.9264456 01-Sep-09 11:49:00 170.5748291 6602.28369 79.743309 1.92649734 01-Sep-09 11:50:00 170.4152069 6601.05029 79.8436737 1.92654896 01-Sep-09 11:51:00 169.3448181 6566.79492 79.9440308 1.92660069 01-Sep-09 11:52:00 169.858139 6575.7666 79.7380371 1.92662179 01-Sep-09 11:53:00 169.4442596 6557.0415 79.8378448 1.92658997 01-Sep-09 11:54:00 169.5765533 6566.59961 79.9376602 1.92655814 01-Sep-09 11:55:00 169.4186707 6569.04395 79.8711166 1.92652619 01-Sep-09 11:56:00 169.074585 6549.24316 79.8093033 1.92649436 01-Sep-09 11:57:00 169.9945984 6563.47021 79.9409866 1.92646253 01-Sep-09 11:58:00 170.7342377 6660.89697 79.7912674 1.9264307 01-Sep-09 11:59:00 170.7524109 6621.44336 79.7080078 1.92639887 01-Sep-09 12:00:00 170.6995544 6603.02295 79.757637 1.92636704 01-Sep-09 12:01:00 170.435379 6608.06396 79.8072739 1.9263351 01-Sep-09 12:02:00 170.405899 6606.84814 79.8569031 1.92630327 01-Sep-09 12:03:00 170.7313385 6605.63281 79.9065399 1.92627144 01-Sep-09 12:04:00 170.6330566 6605.49219 79.9561768 1.92623961 01-Sep-09 12:05:00 171.0271301 6610.36865 79.935997 1.92620778 01-Sep-09 12:06:00 170.286087 6580.04443 79.7463531 1.92617583 01-Sep-09 12:07:00 170.4086609 6606.33545 79.9451447 1.926144 01-Sep-09 12:08:00 170.5242462 6598.63477 79.4253082 1.92611217 01-Sep-09 12:09:00 170.2277832 6589.16895 79.4567566 1.92608035 01-Sep-09 12:10:00 169.5926666 6568.26758 79.9958801 1.92604852 01-Sep-09 12:11:00 170.0024414 6579.00879 80.3005829 1.92601669 01-Sep-09 12:12:00 169.3649597 6573.90381 80.1996231 1.92598474 01-Sep-09 12:13:00 170.1666412 6568.79834 80.0986633 1.92595291 01-Sep-09 12:14:00 169.9733276 6566.62354 79.9977036 1.92592108 01-Sep-09 12:15:00 170.261734 6587.67139 79.8967438 1.92588925 01-Sep-09 12:16:00 170.657959 6581.66797 79.795784 1.92585742 01-Sep-09 12:17:00 170.4340057 6593.56885 79.6948242 1.92582548 01-Sep-09 12:18:00 170.0708008 6641.01416 79.6657944 1.92579365 01-Sep-09 12:19:00 170.069046 6617.36328 79.4136963 1.92576182 01-Sep-09 12:20:00 170.4230652 6596.10791 79.6549301 1.92572999 01-Sep-09 12:21:00 169.9980164 6592.99121 79.4911499 1.92569816 01-Sep-09 12:22:00 170.184433 6591.82129 79.6213074 1.92566621 01-Sep-09 12:23:00 170.8148193 6603.63672 79.7514725 1.92563438 01-Sep-09 12:24:00 170.5036774 6599.625 79.8816299 1.92560256 01-Sep-09 12:25:00 169.6221924 6572.49072 80.011795 1.92557073



### Page 3 of 4Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 01-Sep-09 12:26:00 169.5121918 6548.5918 80.1419601 1.9255389 01-Sep-09 12:27:00 169.771225 6558.25146 80.2721176 1.92550707 01-Sep-09 12:28:00 169.5052948 6593.73389 80.2469559 1.92547512 01-Sep-09 12:29:00 169.5639496 6575.1499 80.1603851 1.92544329 01-Sep-09 12:30:00 170.1222992 6591.19141 80.0738144 1.92541146 01-Sep-09 12:31:00 170.1042633 6582.94141 79.9872437 1.92537963 01-Sep-09 12:32:00 169.6146393 6551.40674 79.9006729 1.92534781 01-Sep-09 12:33:00 169.1250153 6562.77344 79.8141022 1.92531586 01-Sep-09 12:34:00 169.594574 6575.2041 79.7275314 1.92528403 01-Sep-09 12:35:00 170.6145935 6594.59473 79.7780838 1.9252522 01-Sep-09 12:36:00 169.974823 6586.69336 79.9265823 1.92522037 01-Sep-09 12:37:00 170.0362701 6559.99268 79.9153748 1.92518854 01-Sep-09 12:38:00 170.4515991 6602.00244 79.7644196 1.92515671 01-Sep-09 12:39:00 170.2804871 6596.05078 79.9586029 1.92512476 01-Sep-09 12:40:00 170.0301361 6608.16846 79.8840485 1.92509294 01-Sep-09 12:41:00 169.5167694 6568.90918 79.8095016 1.92506111 01-Sep-09 12:42:00 169.1091766 6575.62939 79.7349472 1.92502928 01-Sep-09 12:43:00 170.4509888 6582.34912 79.8711166 1.92499745 01-Sep-09 12:44:00 170.5572662 6589.06885 79.8810959 1.9249655 01-Sep-09 12:45:00 170.753952 6591.47021 79.7160721 1.92493367 01-Sep-09 12:46:00 169.8368225 6564.05713 79.7831955 1.92490184 01-Sep-09 12:47:00 169.5136719 6564.48926 79.8503189 1.92487001 01-Sep-09 12:48:00 169.8128967 6580.44189 79.9174423 1.92483819 01-Sep-09 12:49:00 170.0007172 6581.95117 79.9845657 1.92480624 01-Sep-09 12:50:00 169.7071381 6567.38232 80.0516891 1.92477441 01-Sep-09 12:51:00 169.9154663 6575.76953 80.1188126 1.92474258 01-Sep-09 12:52:00 170.4890594 6584.15625 80.185936 1.92471075 01-Sep-09 12:53:00 170.5772095 6589.35791 80.2530594 1.92467892 01-Sep-09 12:54:00 169.4154663 6569.92383 80.2987671 1.92464709 01-Sep-09 12:55:00 170.4129181 6584.48096 80.2373734 1.92461514 01-Sep-09 12:56:00 169.9683075 6578.24756 80.175972 1.92458332 01-Sep-09 12:57:00 169.621994 6572.01416 80.1145782 1.92455149 01-Sep-09 12:58:00 169.2756805 6565.78076 80.0531845 1.92451966



### Page 4 of 4

## APPENDIX C

FUEL ANALYSIS

# UNIT 1 HRSG ACID MIST STACK TEST 08/27/2009

Calibration Standard Check

% CO2 % A r % N2 % CO % H2 % H2S/COS True Value 15.10 1.00 2.99 43.90 36.90 N.A. Std. 1 15.09 1.02 3.00 43.94 36.95 N.A. Std. 2 15.08 1.02 2.99 43.70 37.21 N.A. Avg. 15.09 1.02 3.00 43.82 37.08 N.A.



# Clean Syngas

Time Sampled % CO2 % Ar2 % N2 % CO % H2 % H2S/COS 820 15.04 0.88 2.30 46.29 35.49 N.A. 820 15.11 0.86 2.89 46.58 35.18 N.A. 930 15.15 0.84 2.53 46.61 34.87 N.A. 930 15.24 0.86 2.25 46.66 34.99 N.A. 1230 15.46 0.86 2.18 46.47 35.03 N.A. 1400 15.40 0.87 2.29 46.69 34.75 N.A. 1400 15.43 0.87 2.28 46.78 34.64 N.A. Avg. 15.26 0.86 2.39 46.58 34.99 0

Mole Wt. 21.48

HH V BTU/SCF 263.71

HH V BTU/Lb 4627Natural Gas and Heatin g Value Calculations Customer: Tampa Electric Company Facility: Polk Power Station Source: Unit 1

CALCULATION OF DENSITY AND HEATING VALUE @ 68°F and 29.92 in H g % volume Component Gross * Volume % Molecular Density * x Gross Weight Heating Value Fract. Component Volume Wt. (lb/ft 3 ) Density weight % Btu/lb Fract. Btu (Btu/SCF) Btu Hydrogen 34.9900 2.016 0.0053 0.00185 3.2608 61100 1992.34 325.0 113.7175 Oxygen 0.0000 32.000 0.0846 0.00000 0.0000 0 0.00 0.0 0 Nitrogen 2.3900 28.014 0.0744 0.00178 3.1266 0 0.00 0.0 0 CO2 15.2600 44.010 0.1170 0.01785 31.3937 0 0.00 0.0 0 CO 46.5800 28.010 0.0740 0.03447 60.6085 4347 2634.65 322.0 149.9876 Argon 0.8600 39.948 0.1065 0.00092 0.1232 0 0.00 0.0 0

T otal: 100.08 Avera g e Density 0.05687 98.5127 Gross Heating Value Specific Gravity 0.74342 Btu/lb 4627 Btu/SCF 263.71

Btu/lb 4325 Btu/SCF 246

* Density (lb/ft 3 ) and Gross Heating Value (Btu/scf) data from Perry's Chemical Engineering Hanbook

. Net Heating Value (Lower Heating Value), Btu/lb, calculated as Gross Heating Value (Higher Heating Value) - 10.30 (%H 2 x 8.94)

CALCULATION OF F FACTORS Weight Percents Componen t Mol. Wt. C Factor H Factor % volume Fract. Wt. Carbon Hydrogen Nitrogen Oxygen Hydrogen 2.016 0 1 34.990 70.5398 3.283753 Oxygen 32.000 0 0 0.000 0.0000 0 Nitrogen 28.014 0 0 2.390 66.9535 3.116800695 CO2 44.010 0.272273 0 15.260 671.5926 8.51229146 22.72879 CO 28.010 0.42587 0 46.580 1304.7058 25.8657841 34.905173 Argon 39.948 0 0 0.860 34.3553

Totals 100.08000 2148.1470 34.3780755 3.28 3.116800695 57.633963 CALCULATED VALUES O2 F Factor (dry), Fd 8316 DSCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air O2 F Factor (wet), Fw 9685 SCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air Moisture F Factor 1370 SCF of Water/MM Btu of Fuel Burned @ 0% excess air Combust. Moisture 14.14 volume % water in flue gas @ 0% excess air CO2 F Factor, Fc 2385 DSCF of CO2/MM Btu of Fuel Burned @ 0% excess air Carbon Dioxide 28.68 volume % CO2 in flue gas @ 0% O2 Predicted Fo Factor 0.73 EPA Method 3a Fo value Net Heating Values

## APPENDIX D

CEMS DATA

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 08/27/2009 7:47 43.14 18.9 8.8 10.3 759.6 08/27/2009 7:48 43.67 19.3 8.8 10.4 771 08/27/2009 7:49 43.94 19.1 8.8 10.4 763.9 08/27/2009 7:50 44.33 18.8 8.8 10.4 753.3 08/27/2009 7:51 44.38 18.8 8.8 10.4 755.3 08/27/2009 7:52 44.26 18.9 8.8 10.4 758.8 08/27/2009 7:53 43.69 18.9 8.8 10.4 761.1 08/27/2009 7:54 44.18 19.1 8.8 10.4 751.9 08/27/2009 7:55 44.32 19.1 8.8 10.4 753.2 08/27/2009 7:56 44.7 18.9 8.8 10.4 760 08/27/2009 7:57 44.98 19.1 8.8 10.4 768.2 08/27/2009 7:58 45.28 19.2 8.8 10.4 767.6 08/27/2009 7:59 44.96 19.1 8.8 10.4 784 08/27/2009 8:00 44.78 19.3 8.8 10.4 764.8 08/27/2009 8:01 43.97 19.6 8.8 10.4 783.8 08/27/2009 8:02 44.23 19.8 8.8 10.4 768.2 08/27/2009 8:03 44.47 19.4 8.8 10.4 762.8 08/27/2009 8:04 44.64 19.3 8.8 10.4 756.2 08/27/2009 8:05 44.24 19.5 8.8 10.4 742.8 08/27/2009 8:06 43.4 19.9 8.8 10.4 753.2 08/27/2009 8:07 43.94 19.8 8.8 10.4 760 08/27/2009 8:08 44.07 20.3 8.8 10.4 765.6 08/27/2009 8:09 44.31 19.7 8.8 10.4 770.6 08/27/2009 8:10 44.03 19.7 8.8 10.4 773.1 08/27/2009 8:11 43.93 19.6 8.8 10.4 762.9 08/27/2009 8:12 44.66 19.6 8.8 10.4 745.9 08/27/2009 8:13 44.09 19.9 8.8 10.4 758 08/27/2009 8:14 44.41 19.7 8.8 10.4 763.3 08/27/2009 8:15 43.93 19.2 8.8 10.4 755.6 08/27/2009 8:16 43.38 19.4 8.8 10.4 757.7 08/27/2009 8:17 43.64 19.6 8.8 10.4 764.8 08/27/2009 8:18 43.86 19.7 8.8 10.4 770.4 08/27/2009 8:19 44.08 19.3 8.8 10.4 764.2 08/27/2009 8:20 44.72 19.5 8.8 10.4 766.7 08/27/2009 8:21 44.99 19.4 8.8 10.4 756.8 08/27/2009 8:22 45 19.3 8.8 10.4 775.3 08/27/2009 8:23 44.89 19.3 8.8 10.4 766.5 08/27/2009 8:24 45.05 19.2 8.8 10.4 764.1 08/27/2009 8:25 44.84 19.3 8.8 10.4 751.7 08/27/2009 8:26 44.96 19.6 8.8 10.4 764.8 08/27/2009 8:27 44.86 19.6 8.8 10.4 771.7 Run 1

Page 1 of 16

### CEMS Data

08/27/2009 8:28 44.64 19.5 8.8 10.4 762.8 08/27/2009 8:29 44.72 19.5 8.8 10.4 766.4 08/27/2009 8:30 44.54 19.8 8.8 10.4 765.5 08/27/2009 8:31 44.4 19.6 8.8 10.4 763 08/27/2009 8:32 44.37 19.2 8.8 10.4 768.5 08/27/2009 8:33 44.61 19.5 8.8 10.4 787.2 08/27/2009 8:34 45.15 19.4 8.8 10.4 780.4 08/27/2009 8:35 45.56 19.4 8.9 10.4 761.1 08/27/2009 8:36 44.66 19.6 8.9 10.4 745.7 08/27/2009 8:37 44.07 19.7 8.9 10.4 768.9 08/27/2009 8:38 44.09 19.6 8.9 10.4 777.8 08/27/2009 8:39 44.43 19.7 8.9 10.4 778 08/27/2009 8:40 44.27 19.5 8.9 10.4 763.9 08/27/2009 8:41 44.78 19.6 8.9 10.4 775.8 08/27/2009 8:42 44.97 19.9 8.9 10.4 776.8 08/27/2009 8:43 45.09 19.6 8.8 10.4 785 08/27/2009 8:44 45.47 19.5 8.8 10.4 787.6 08/27/2009 8:45 44.74 19.1 8.8 10.4 781 08/27/2009 8:46 43.75 19.4 8.8 10.4 770.3 08/27/2009 8:47 43.79 19.7 8.8 10.5 764.5 08/27/2009 8:48 43.74 20.2 8.8 10.5 756.7 08/27/2009 8:49 44.11 20.2 8.8 10.5 773.3 08/27/2009 8:50 44.25 20 8.8 10.4 766.8 08/27/2009 8:51 44.34 19.6 8.8 10.5 788.1 08/27/2009 8:52 44.58 19.6 8.8 10.5 759.6 08/27/2009 8:53 44.48 19.8 8.8 10.5 777.8 08/27/2009 8:54 44.11 19.8 8.8 10.4 770 08/27/2009 8:55 44.48 20.1 8.9 10.5 780.1 08/27/2009 8:56 44.08 20.2 8.8 10.4 782.7 08/27/2009 8:57 44.46 20 8.8 10.4 782.8 44.39 19.51 8.81 10.41 766.73 766725.4 724870.752

Page 2 of 16

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 08/27/2009 9:30 44.16 20.9 8.9 10.5 771.4 08/27/2009 9:31 44 20.7 8.9 10.5 770.9 08/27/2009 9:32 43.64 20.3 8.9 10.5 771.2 08/27/2009 9:33 43.76 20.5 8.8 10.5 772.4 08/27/2009 9:34 44.17 20.1 8.8 10.4 780.8 08/27/2009 9:35 43.94 19.6 8.8 10.4 779 08/27/2009 9:36 43.15 19.9 8.8 10.5 783.7 08/27/2009 9:37 43.34 20 8.8 10.5 790.8 08/27/2009 9:38 43.33 20.4 8.8 10.5 784.8 08/27/2009 9:39 43.82 20.2 8.8 10.5 783.5 08/27/2009 9:40 43.91 20.3 8.9 10.5 773.6 08/27/2009 9:41 44.06 20.1 8.8 10.5 779.5 08/27/2009 9:42 44.1 20.4 8.9 10.4 777.6 08/27/2009 9:43 44.52 20.2 8.9 10.4 759.4 08/27/2009 9:44 44.35 20.4 8.9 10.5 762.5 08/27/2009 9:45 44.04 20.3 8.8 10.5 767.8 08/27/2009 9:46 44.06 20.3 8.9 10.5 766.8 08/27/2009 9:47 44.17 20.5 8.9 10.5 762.4 08/27/2009 9:48 43.8 20.2 8.8 10.5 773.5 08/27/2009 9:49 43.41 20 8.8 10.5 781 08/27/2009 9:50 43.54 20.6 8.9 10.5 781.1 08/27/2009 9:51 43.62 20.4 8.9 10.5 784.5 08/27/2009 9:52 44.04 20.3 8.9 10.5 753.6 08/27/2009 9:53 43.71 20.3 8.9 10.5 771.4 08/27/2009 9:54 43.51 20.3 8.9 10.5 764.8 08/27/2009 9:55 42.9 20 8.9 10.5 779.4 08/27/2009 9:56 42.93 20.1 8.9 10.5 773.4 08/27/2009 9:57 43.4 20.3 8.9 10.5 774.2 08/27/2009 9:58 43.16 20.5 8.9 10.5 761 08/27/2009 9:59 43.48 20.5 8.9 10.5 750 08/27/2009 10:00 43.61 20.5 8.9 10.5 761.8 08/27/2009 10:01 43.52 20.5 8.9 10.5 769.4 08/27/2009 10:02 43.78 20.8 8.9 10.5 775.9 08/27/2009 10:03 44.33 20.8 8.8 10.5 775.5 08/27/2009 10:04 44.83 20.6 8.8 10.5 783.7 08/27/2009 10:05 44.98 20 8.8 10.5 782.8 08/27/2009 10:06 43.96 20.2 8.8 10.6 771.6 08/27/2009 10:07 43.19 20.8 8.9 10.5 765.2 08/27/2009 10:08 43.51 21.1 8.9 10.5 780 08/27/2009 10:09 43.74 21.2 8.9 10.5 760.4 08/27/2009 10:10 43.71 21.1 8.9 10.5 767.1 Run 2

Page 3 of 16

### CEMS Data

08/27/2009 10:11 44.25 21.4 8.9 10.5 790.5 08/27/2009 10:12 43.42 20.9 8.9 10.5 782.2 08/27/2009 10:13 43.96 20.7 8.8 10.6 767.1 08/27/2009 10:14 44.19 21.1 8.8 10.5 762.7 08/27/2009 10:15 44.6 20.9 8.8 10.5 759.6 08/27/2009 10:16 44.59 20.7 8.9 10.5 773.5 08/27/2009 10:17 44.51 21.2 8.9 10.5 761.5 08/27/2009 10:18 44.29 21.1 8.8 10.5 777.4 08/27/2009 10:19 44.3 21.2 8.9 10.5 771.8 08/27/2009 10:20 44.43 20.7 8.9 10.5 770.1 08/27/2009 10:21 44.49 20.9 8.8 10.5 766.5 08/27/2009 10:22 44.89 21 8.8 10.6 763.5 08/27/2009 10:23 44.64 21.1 8.8 10.5 776.3 08/27/2009 10:24 44.28 20.9 8.9 10.5 755.9 08/27/2009 10:25 44.06 20.3 8.9 10.4 756.1 08/27/2009 10:26 43.62 20.2 8.9 10.5 767 08/27/2009 10:27 43.8 20.6 8.9 10.5 762.2 08/27/2009 10:28 44.41 20.5 8.9 10.4 766.4 08/27/2009 10:29 44.43 20.6 8.9 10.5 760.1 08/27/2009 10:30 44.9 20.6 8.9 10.5 765.8 08/27/2009 10:31 45.23 20.5 8.8 10.5 771.5 08/27/2009 10:32 44.63 20.4 8.9 10.5 775.8 08/27/2009 10:33 44.26 20.1 8.9 10.4 774.2 08/27/2009 10:34 44.39 20 8.9 10.5 775.2 08/27/2009 10:35 44.54 20.4 8.9 10.5 781.7 08/27/2009 10:36 44.56 20.3 8.9 10.5 766.7 08/27/2009 10:37 44.45 20.5 8.9 10.5 767.5 08/27/2009 10:38 44.16 20 8.8 10.5 765.3 08/27/2009 10:39 44.94 19.8 8.8 10.5 773.9 44.03 20.50 8.86 10.49 771.25 771248.6 719169.55

Page 4 of 16

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 08/27/2009 10:58 46.07 20.2 8.9 10.5 767.5 08/27/2009 10:59 46.68 20 8.8 10.5 786.1 08/27/2009 11:00 46.24 19.7 8.9 10.5 759.1 08/27/2009 11:01 46.9 19.7 8.8 10.5 771.3 08/27/2009 11:02 46.43 20.2 8.9 10.5 761.4 08/27/2009 11:03 45.92 20.5 8.9 10.5 773.5 08/27/2009 11:04 46.25 19.9 8.9 10.5 779.9 08/27/2009 11:05 45.78 19.8 8.9 10.5 781.2 08/27/2009 11:06 45.53 19.9 8.9 10.5 780.4 08/27/2009 11:07 46 19.8 8.8 10.5 766 08/27/2009 11:08 46.14 19.9 8.9 10.5 783.4 08/27/2009 11:09 46.35 19.8 8.8 10.5 790.9 08/27/2009 11:10 46.57 19.8 8.8 10.5 790.6 08/27/2009 11:11 46.37 19.9 8.9 10.4 778.1 08/27/2009 11:12 46.2 19.9 8.9 10.5 761.5 08/27/2009 11:13 46.3 20.1 8.9 10.5 753.2 08/27/2009 11:14 45.91 19.9 8.9 10.5 764.3 08/27/2009 11:15 45.5 19.2 8.9 10.4 793.9 08/27/2009 11:16 45.27 19.6 8.9 10.5 791.9 08/27/2009 11:17 45.19 20 8.9 10.5 781.7 08/27/2009 11:18 45.8 19.9 8.9 10.5 766 08/27/2009 11:19 46.53 19.4 8.9 10.5 767.4 08/27/2009 11:20 46.88 19.5 8.9 10.5 763.8 08/27/2009 11:21 46.34 19.6 8.9 10.5 766.7 08/27/2009 11:22 46.45 19.9 8.9 10.5 767.9 08/27/2009 11:23 46.67 20 8.9 10.5 784.4 08/27/2009 11:24 47.01 19.6 8.9 10.4 763.8 08/27/2009 11:25 46.77 19.4 8.9 10.4 766.8 08/27/2009 11:26 45.8 19.4 8.9 10.5 758.1 08/27/2009 11:27 46.1 19.6 8.9 10.5 751.3 08/27/2009 11:28 46.8 19.8 8.9 10.5 758.2 08/27/2009 11:29 46.92 19.9 8.9 10.5 763.5 08/27/2009 11:30 47.04 20 8.9 10.5 761.5 08/27/2009 11:31 46.38 19.8 8.9 10.5 756.2 08/27/2009 11:32 46.51 19.6 8.9 10.5 771.1 08/27/2009 11:33 46.44 19.8 8.9 10.5 772.7 08/27/2009 11:34 45.69 19.5 8.9 10.5 774.1 08/27/2009 11:35 46.28 19.7 8.9 10.5 771.2 08/27/2009 11:36 46.45 19.7 8.8 10.5 769.8 08/27/2009 11:37 46.5 19.6 8.9 10.5 760.4 08/27/2009 11:38 47.11 19.8 8.9 10.5 769 Run 3

Page 5 of 16

### CEMS Data

08/27/2009 11:39 47.06 19.6 8.8 10.5 777 08/27/2009 11:40 46.86 19.9 8.9 10.5 769.5 08/27/2009 11:41 46.56 19.9 8.8 10.5 783.5 08/27/2009 11:42 45.98 20 8.8 10.5 767.7 08/27/2009 11:43 45.42 20 8.8 10.5 801 08/27/2009 11:44 45.62 20.2 8.8 10.4 778 08/27/2009 11:45 45.41 19.6 8.9 10.4 766.8 08/27/2009 11:46 45.14 19.3 8.8 10.4 774 08/27/2009 11:47 45.71 19.3 8.8 10.4 763.6 08/27/2009 11:48 46.19 19.2 8.8 10.5 764.1 08/27/2009 11:49 46.39 19.4 8.8 10.5 761 08/27/2009 11:50 46.71 19.5 8.9 10.4 777.3 08/27/2009 11:51 47.01 19.3 8.9 10.4 777.1 08/27/2009 11:52 47.76 19.3 8.9 10.4 762.3 08/27/2009 11:53 47.94 19.2 8.9 10.4 777.1 08/27/2009 11:54 47.78 19.4 8.9 10.4 768.1 08/27/2009 11:55 47.73 19.6 8.9 10.4 765.2 08/27/2009 11:56 46.97 19.3 8.9 10.4 780 08/27/2009 11:57 46.46 19.7 8.9 10.4 774.9 08/27/2009 11:58 45.13 20 8.9 10.4 770.5 08/27/2009 11:59 45.08 19.7 8.9 10.4 765.4 08/27/2009 12:00 44.87 19.5 8.9 10.5 763.2 08/27/2009 12:01 44.28 19.6 8.9 10.4 768.8 08/27/2009 12:02 43.97 20 8.9 10.4 784.1 08/27/2009 12:03 43.48 20.1 8.9 10.4 773.8 08/27/2009 12:04 43.82 20 8.9 10.4 779.6 08/27/2009 12:05 43.79 19.8 8.9 10.4 780.9 08/27/2009 12:06 43.98 19.6 8.9 10.4 769.8 46.10 19.73 8.88 10.47 771.65 771653.6 720832.834

Page 6 of 16

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 08/27/2009 12:25 42.74 19.8 8.8 10.5 772.9 08/27/2009 12:26 40.31 14.4 4.8 10.5 753.5 08/27/2009 12:27 6.94 0.2 0 10.5 773.6 08/27/2009 12:28 18.89 11.4 7.6 10.5 769.1 08/27/2009 12:29 40.48 18.7 8.8 10.5 765.8 08/27/2009 12:30 42.81 19.5 8.8 10.5 768.8 08/27/2009 12:31 43.14 19.5 8.8 10.5 758.6 08/27/2009 12:32 42.53 19.7 8.8 10.5 779.1 08/27/2009 12:33 42.5 19.7 8.8 10.5 773.9 08/27/2009 12:34 43.32 19.7 8.8 10.5 774.1 08/27/2009 12:35 43.51 19.3 8.8 10.5 781.6 08/27/2009 12:36 43.33 19.6 8.8 10.5 766.3 08/27/2009 12:37 43.02 19.8 8.8 10.5 768 08/27/2009 12:38 43.06 19.9 8.8 10.5 776.2 08/27/2009 12:39 43.34 19.7 8.8 10.5 756.6 08/27/2009 12:40 43.56 19.8 8.8 10.5 741.5 08/27/2009 12:41 43.29 19.7 8.8 10.5 762.6 08/27/2009 12:42 43.19 19.9 8.8 10.5 771 08/27/2009 12:43 42.84 19.7 8.8 10.5 773.8 08/27/2009 12:44 43.57 19.7 8.8 10.4 774.4 08/27/2009 12:45 43.32 19.1 8.8 10.4 772.3 08/27/2009 12:46 43.2 19.3 8.8 10.5 771.1 08/27/2009 12:47 43.28 19.4 8.8 10.5 776 08/27/2009 12:48 43.26 19.5 8.8 10.5 774.7 08/27/2009 12:49 43.31 19.7 8.8 10.5 763.7 08/27/2009 12:50 43.02 19.7 8.8 10.4 777.6 08/27/2009 12:51 43.26 19.5 8.8 10.4 811.3 08/27/2009 12:52 43.29 19.7 8.8 10.5 770.8 08/27/2009 12:53 43.2 19.4 8.8 10.4 770.6 08/27/2009 12:54 43.75 19.2 8.8 10.5 760.2 08/27/2009 12:55 43.7 19.3 8.8 10.5 781.1 08/27/2009 12:56 43.34 19.3 8.8 10.5 773.5 08/27/2009 12:57 43.09 19.6 8.8 10.5 775.4 08/27/2009 12:58 42.83 19.7 8.8 10.4 787.9 08/27/2009 12:59 42.93 19.5 8.8 10.5 799.9 08/27/2009 13:00 42.83 19.5 8.8 10.5 764.2 08/27/2009 13:01 42.95 19.7 8.8 10.5 783.1 08/27/2009 13:02 43.37 19.4 8.8 10.5 785 08/27/2009 13:03 43.03 19.5 8.8 10.4 780.3 08/27/2009 13:04 42.76 19.3 8.8 10.4 760.5 08/27/2009 13:05 43.5 19.3 8.9 10.4 767 Run 4

Page 7 of 16

### CEMS Data

08/27/2009 13:06 42.56 19.1 8.8 10.4 775.3 08/27/2009 13:07 43.05 19.4 8.8 10.4 763.4 08/27/2009 13:08 42.54 19.4 8.8 10.4 748 08/27/2009 13:09 42.66 19.1 8.8 10.4 754.7 08/27/2009 13:10 43.12 19.2 8.8 10.4 774.6 08/27/2009 13:11 43.15 19.5 8.8 10.4 769.7 08/27/2009 13:12 43.08 19.9 8.9 10.5 771.4 08/27/2009 13:13 43.08 19.5 8.8 10.4 775.6 08/27/2009 13:14 43.8 19.4 8.8 10.4 776.5 08/27/2009 13:15 44.01 19.6 8.8 10.5 783.3 08/27/2009 13:16 44.07 19.8 8.8 10.5 780.1 08/27/2009 13:17 44.19 19.7 8.8 10.5 760.2 08/27/2009 13:18 43.78 20 8.8 10.5 762.5 08/27/2009 13:19 43.24 20 8.8 10.5 780.8 08/27/2009 13:20 42.8 19.9 8.8 10.5 785.1 08/27/2009 13:21 43.17 19.8 8.8 10.5 775.7 08/27/2009 13:22 43.33 19.8 8.8 10.5 767.5 08/27/2009 13:23 42.95 19.9 8.8 10.5 765.7 08/27/2009 13:24 43.52 20.2 8.8 10.5 785.4 08/27/2009 13:25 43.52 20 8.9 10.4 765.6 08/27/2009 13:26 42.34 20.1 8.9 10.5 766.3 08/27/2009 13:27 42.12 20 8.8 10.5 770.5 08/27/2009 13:28 43 19.9 8.8 10.5 781.3 08/27/2009 13:29 43.13 20 8.8 10.5 792.8 08/27/2009 13:30 43.37 20.2 8.8 10.5 791.5 08/27/2009 13:31 43.37 20.2 8.8 10.5 780.2 08/27/2009 13:32 43.69 20 8.8 10.5 775.4 08/27/2009 13:33 43.36 19.9 8.8 10.4 758.2 42.23 19.16 8.60 10.47 772.53 772534.8 679950.986

Page 8 of 16

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 08/27/2009 15:24 43.87 20.3 8.8 10.5 764.8 08/27/2009 15:25 43.26 19.6 8.8 10.5 751.9 08/27/2009 15:26 42.71 19.8 8.8 10.5 753.1 08/27/2009 15:27 42.31 20.5 8.8 10.5 762.2 08/27/2009 15:28 42.78 20.6 8.8 10.5 762.5 08/27/2009 15:29 43.28 20.4 8.8 10.5 777.3 08/27/2009 15:30 43.46 20.2 8.8 10.5 763.6 08/27/2009 15:31 43.15 20.3 8.8 10.5 767 08/27/2009 15:32 42.96 20.4 8.8 10.5 768.1 08/27/2009 15:33 42.95 20.6 8.8 10.5 778.1 08/27/2009 15:34 43.06 20.9 8.8 10.5 779 08/27/2009 15:35 43.09 20.3 8.8 10.5 767.6 08/27/2009 15:36 43.13 20.4 8.8 10.5 785.4 08/27/2009 15:37 42.97 20.4 8.8 10.5 784.4 08/27/2009 15:38 42.96 20.5 8.8 10.5 771.6 08/27/2009 15:39 42.97 20.7 8.8 10.5 755 08/27/2009 15:40 42.61 20.7 8.8 10.5 770.8 08/27/2009 15:41 42.28 20.7 8.8 10.5 761.3 08/27/2009 15:42 42.6 20.5 8.8 10.5 767.2 08/27/2009 15:43 42.42 20.2 8.8 10.5 771.2 08/27/2009 15:44 43.15 19.8 8.8 10.5 778.8 08/27/2009 15:45 43.63 19.8 8.8 10.4 763.9 08/27/2009 15:46 43.47 19.7 8.8 10.5 766.7 08/27/2009 15:47 43.2 20.2 8.8 10.5 759.6 08/27/2009 15:48 43.4 20.6 8.8 10.5 775 08/27/2009 15:49 43.27 20.9 8.8 10.5 779.4 08/27/2009 15:50 43.69 20.5 8.8 10.5 781.3 08/27/2009 15:51 43.14 20.2 8.8 10.5 776.6 08/27/2009 15:52 43.26 20.3 8.8 10.5 751.9 08/27/2009 15:53 43.47 20.8 8.8 10.5 768.8 08/27/2009 15:54 43.28 21.1 8.8 10.5 783 08/27/2009 15:55 43.3 20.7 8.8 10.5 780.1 08/27/2009 15:56 42.84 20.8 8.8 10.5 775.2 08/27/2009 15:57 42.89 21.2 8.8 10.6 773.3 08/27/2009 15:58 42.5 21.1 8.8 10.5 776.5 08/27/2009 15:59 42.01 20.9 8.8 10.5 777.2 08/27/2009 16:00 41.71 21 8.8 10.6 778.2 08/27/2009 16:01 41.34 21.4 8.8 10.6 783.1 08/27/2009 16:02 40.94 21.4 8.8 10.6 767.6 08/27/2009 16:03 40.78 21.5 8.8 10.6 777.7 08/27/2009 16:04 41.21 21.3 8.8 10.5 774.5 Run 5

Page 9 of 16

### CEMS Data

08/27/2009 16:05 41.31 21.2 8.8 10.5 767.8 08/27/2009 16:06 41.06 21 8.8 10.6 777.7 08/27/2009 16:07 41.05 21.2 8.8 10.6 769.5 08/27/2009 16:08 41.79 21.4 8.8 10.6 774.2 08/27/2009 16:09 42.04 21.9 8.9 10.6 778.1 08/27/2009 16:10 41.48 21.7 8.8 10.6 774.4 08/27/2009 16:11 41.9 21.3 8.8 10.6 759.5 08/27/2009 16:12 41.46 21.4 8.8 10.6 773.3 08/27/2009 16:13 41.38 21.5 8.8 10.6 775.6 08/27/2009 16:14 41.81 21.6 8.8 10.6 771.2 08/27/2009 16:15 42.21 21 8.8 10.5 766.7 08/27/2009 16:16 41.61 20.5 8.8 10.6 785.8 08/27/2009 16:17 41.9 21.1 8.8 10.6 762.4 08/27/2009 16:18 41.66 21.1 8.8 10.6 786.9 08/27/2009 16:19 41.92 21 8.8 10.6 758.7 08/27/2009 16:20 41.8 21 8.8 10.6 776.7 08/27/2009 16:21 41.91 21 8.8 10.5 795.2 08/27/2009 16:22 42.4 20.9 8.8 10.6 781.8 08/27/2009 16:23 42.9 20.7 8.8 10.5 776.3 08/27/2009 16:24 42.83 20.9 8.8 10.5 772.2 08/27/2009 16:25 42.25 20.9 8.8 10.5 769.7 08/27/2009 16:26 42.08 21.1 8.8 10.5 770.1 08/27/2009 16:27 42.73 20.8 8.8 10.5 786.5 08/27/2009 16:28 42.76 20.7 8.8 10.5 779.5 08/27/2009 16:29 42.59 20.5 8.8 10.5 769.6 08/27/2009 16:30 42.64 20.8 8.8 10.5 781.6 08/27/2009 16:31 42.11 20.8 8.8 10.5 771.8 08/27/2009 16:32 42.07 20.9 8.8 10.5 785.5 42.477536 20.77 8.801 10.53 772.591304 772591.3 690705.595

Page 10 of 16

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 08/27/2009 16:45 43.02 20.3 8.8 10.5 763.4 08/27/2009 16:46 42.09 20.4 8.8 10.5 792.4 08/27/2009 16:47 41.35 20.8 8.8 10.6 775.1 08/27/2009 16:48 41.52 21.3 8.8 10.5 763.5 08/27/2009 16:49 41.61 21.1 8.8 10.5 756.3 08/27/2009 16:50 42.01 21.1 8.8 10.6 771.6 08/27/2009 16:51 41.85 20.9 8.8 10.6 783 08/27/2009 16:52 41.58 21.1 8.8 10.6 798.6 08/27/2009 16:53 41.33 20.9 8.8 10.6 784 08/27/2009 16:54 41.44 21.1 8.8 10.6 770.7 08/27/2009 16:55 41.13 21.3 8.8 10.6 778.7 08/27/2009 16:56 41.28 21.2 8.8 10.6 780.7 08/27/2009 16:57 40.47 21.2 8.8 10.6 765.9 08/27/2009 16:58 40.77 21.5 8.8 10.6 766.1 08/27/2009 16:59 40.89 21.4 8.8 10.6 766 08/27/2009 17:00 41.21 21.3 8.8 10.6 776.9 08/27/2009 17:01 41.54 21 8.8 10.5 761.4 08/27/2009 17:02 41.51 20.8 8.8 10.5 766.8 08/27/2009 17:03 41.34 20.7 8.8 10.5 779.8 08/27/2009 17:04 42.01 20.8 8.8 10.5 760.8 08/27/2009 17:05 42.07 20.3 8.8 10.5 738.9 08/27/2009 17:06 41.6 20.4 8.8 10.5 770.6 08/27/2009 17:07 41.34 20.7 8.8 10.5 780.4 08/27/2009 17:08 41.19 20.7 8.8 10.5 762.9 08/27/2009 17:09 41.74 20.9 8.8 10.5 773.6 08/27/2009 17:10 42.15 21.2 8.8 10.5 778.4 08/27/2009 17:11 41.86 21.4 8.8 10.5 777.8 08/27/2009 17:12 41.75 20.9 8.8 10.6 763.7 08/27/2009 17:13 42.62 21.1 8.8 10.6 789 08/27/2009 17:14 42.53 21.2 8.8 10.5 795.8 08/27/2009 17:15 41.76 21.1 8.8 10.5 773.1 08/27/2009 17:16 41.64 21.4 8.8 10.5 782.5 08/27/2009 17:17 41.37 21.5 8.8 10.5 781.5 08/27/2009 17:18 41.6 21.5 8.8 10.5 772.7 08/27/2009 17:19 41.57 21.3 8.8 10.5 761.6 08/27/2009 17:20 41.52 21.3 8.8 10.5 764.5 08/27/2009 17:21 41.74 21.4 8.8 10.5 774.1 08/27/2009 17:22 41.65 21.5 8.8 10.5 761.5 08/27/2009 17:23 42.03 21.5 8.8 10.5 772.8 08/27/2009 17:24 42.14 21.2 8.8 10.5 783.6 08/27/2009 17:25 42.05 21.1 8.8 10.5 782.4 Run 6

Page 11 of 16

### CEMS Data

08/27/2009 17:26 41.7 21.2 8.8 10.5 777 08/27/2009 17:27 41.3 21.4 8.8 10.5 777.1 08/27/2009 17:28 41.06 21.1 8.8 10.5 777.8 08/27/2009 17:29 40.9 21.2 8.8 10.6 788.3 08/27/2009 17:30 41.03 21.7 8.8 10.5 778.8 08/27/2009 17:31 40.99 21.7 8.8 10.5 777.3 08/27/2009 17:32 41.13 21.4 8.8 10.5 768.4 08/27/2009 17:33 41.58 21.6 8.8 10.5 761.2 08/27/2009 17:34 41.08 21.7 8.8 10.5 767 08/27/2009 17:35 41.06 21.1 8.8 10.5 766 41.56 21.14 8.80 10.53 773.37 773372.549 716724.554 Average for test da y 43.47 20.13 8.79 10.48 771.35 771354.364 708709.045

Page 12 of 16

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 09/01/2009 9:32 45.5 17.5 8.8 10.3 779.5 09/01/2009 9:33 45.58 17.6 8.8 10.4 768 09/01/2009 9:34 45.5 17.6 8.8 10.4 775.6 09/01/2009 9:35 44.95 17.6 8.8 10.4 786.4 09/01/2009 9:36 45.08 18 8.8 10.4 768.4 09/01/2009 9:37 44.65 17.9 8.8 10.4 794.8 09/01/2009 9:38 44.28 17.8 8.8 10.4 771.3 09/01/2009 9:39 44.12 17.5 8.7 10.3 769.8 09/01/2009 9:40 43.33 17.2 8.7 10.3 765 09/01/2009 9:41 42.24 17.4 8.7 10.3 798.6 09/01/2009 9:42 41.38 17.5 8.7 10.4 799.8 09/01/2009 9:43 41.6 17.5 8.7 10.3 790.8 09/01/2009 9:44 41.19 17.7 8.7 10.4 782.5 09/01/2009 9:45 40.34 17.7 8.7 10.4 780.4 09/01/2009 9:46 39.49 17.7 8.7 10.4 774 09/01/2009 9:47 38.71 17.6 8.7 10.4 767.4 09/01/2009 9:48 37.81 17.6 8.7 10.4 774 09/01/2009 9:49 37.35 17.5 8.7 10.4 779.1 09/01/2009 9:50 36.79 17.4 8.7 10.4 773.9 09/01/2009 9:51 36.7 17.5 8.7 10.4 765.6 09/01/2009 9:52 35.78 17.4 8.7 10.4 769.3 09/01/2009 9:53 36.06 17.4 8.7 10.4 774 09/01/2009 9:54 35.91 17.5 8.7 10.3 788.8 09/01/2009 9:55 36.5 17.6 8.7 10.3 781.9 09/01/2009 9:56 37.11 17.4 8.7 10.3 777.2 09/01/2009 9:57 37.49 17.5 8.7 10.3 777.7 09/01/2009 9:58 38.03 17.4 8.7 10.4 786.3 09/01/2009 9:59 38.63 17.5 8.7 10.3 782.6 09/01/2009 10:00 38.58 17.5 8.7 10.3 787.4 09/01/2009 10:01 38.71 17.5 8.7 10.3 781.8 09/01/2009 10:02 39.33 17.3 8.7 10.4 777.2 09/01/2009 10:03 39.45 17.3 8.7 10.4 780.8 09/01/2009 10:04 40.26 17.3 8.7 10.3 778.8 09/01/2009 10:05 40.93 17.4 8.7 10.3 770.6 09/01/2009 10:06 41.03 17.3 8.7 10.3 776 09/01/2009 10:07 41.53 17.5 8.7 10.4 769.2 09/01/2009 10:08 41.71 17.3 8.7 10.3 757.9 09/01/2009 10:09 42.01 17.1 8.7 10.3 771 09/01/2009 10:10 41.69 16.7 8.7 10.3 763.3 09/01/2009 10:11 40.87 17.2 8.7 10.3 775.3 09/01/2009 10:12 40.48 17.6 8.7 10.3 779.8 Run 7

Page 13 of 16

### CEMS Data

09/01/2009 10:13 40.5 17.4 8.7 10.4 784.3 09/01/2009 10:14 41.05 17.3 8.7 10.4 768.1 09/01/2009 10:15 40.94 17.1 8.7 10.4 764.9 09/01/2009 10:16 40.77 17.3 8.7 10.4 768 09/01/2009 10:17 40.6 17.3 8.7 10.3 771 09/01/2009 10:18 40.37 17.1 8.7 10.4 765 09/01/2009 10:19 40.27 17.2 8.7 10.3 772 09/01/2009 10:20 40.65 17.3 8.7 10.3 794.4 09/01/2009 10:21 40.24 17.2 8.7 10.4 775.1 09/01/2009 10:22 40.08 17.2 8.7 10.4 770.5 09/01/2009 10:23 40.07 17.1 8.7 10.4 757.8 09/01/2009 10:24 39.71 17.1 8.7 10.4 763.8 09/01/2009 10:25 39.97 17.2 8.7 10.4 764.8 09/01/2009 10:26 39.53 17.2 8.7 10.4 760.7 09/01/2009 10:27 39.34 17.4 8.8 10.4 768.6 09/01/2009 10:28 39.46 17.4 8.8 10.4 786.6 09/01/2009 10:29 39.88 17.2 8.7 10.3 779.8 09/01/2009 10:30 40.01 16.9 8.7 10.4 770.9 09/01/2009 10:31 39.83 17.3 8.8 10.4 761.7 09/01/2009 10:32 40.27 17.3 8.8 10.4 779.2 09/01/2009 10:33 40.45 17.4 8.8 10.3 776.8 09/01/2009 10:34 40.83 17.4 8.8 10.3 772.3 09/01/2009 10:35 40.68 17.1 8.8 10.3 771.6 09/01/2009 10:36 40.4 16.8 8.8 10.3 776.8 09/01/2009 10:37 40.59 16.8 8.8 10.3 776.3 40.381364 17.37 8.724 10.36 775.345455 775345.455 704039.863

Page 14 of 16

### CEMS Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

09/01/2009 10:51 39.59 17.3 8.8 10.4 769.3 09/01/2009 10:52 39.96 17.3 8.8 10.4 769 09/01/2009 10:53 40.25 17.5 8.8 10.4 771.5 09/01/2009 10:54 40.37 17.5 8.8 10.4 778.5 09/01/2009 10:55 39.86 17.5 8.8 10.4 759.9 09/01/2009 10:56 39.62 17.6 8.8 10.4 775.9 09/01/2009 10:57 39.72 17.5 8.8 10.4 774 09/01/2009 10:58 39.73 17.3 8.8 10.4 773.4 09/01/2009 10:59 40.01 17.6 8.8 10.3 770 09/01/2009 11:00 39.81 17.2 8.8 10.3 768.4 09/01/2009 11:01 39.22 17.4 8.8 10.4 776.4 09/01/2009 11:02 39.93 17.4 8.8 10.3 767.8 09/01/2009 11:03 40.21 17.6 8.8 10.4 768.4 09/01/2009 11:04 40.26 17.6 8.8 10.4 768.1 09/01/2009 11:05 40.73 17.6 8.8 10.4 765.6 09/01/2009 11:06 40.95 17.5 8.8 10.4 774.2 09/01/2009 11:07 41.24 17.4 8.8 10.4 762.4 09/01/2009 11:08 41.37 17.2 8.8 10.4 760.5 09/01/2009 11:09 40.68 17.3 8.8 10.4 761.1 09/01/2009 11:10 40.63 17.4 8.8 10.4 756.4 09/01/2009 11:11 40.43 17.4 8.8 10.4 754.6 09/01/2009 11:12 40.41 17.3 8.8 10.4 759.2 09/01/2009 11:13 40.49 17.2 8.8 10.4 770.3 09/01/2009 11:14 40.03 17.3 8.8 10.3 768.7 09/01/2009 11:15 39.81 17.3 8.8 10.4 769.5 09/01/2009 11:16 39.83 17.3 8.8 10.4 773.7 09/01/2009 11:17 39.89 17.5 8.8 10.4 771.3 09/01/2009 11:18 39.69 17.3 8.8 10.4 766.5 09/01/2009 11:19 39.93 17.3 8.8 10.3 760.7 09/01/2009 11:20 40.21 17 8.8 10.4 755.2 09/01/2009 11:21 40.03 17.1 8.8 10.4 755.7 09/01/2009 11:22 40.35 17.3 8.8 10.4 770.3 09/01/2009 11:23 40.59 17.2 8.9 10.4 771.4 09/01/2009 11:24 40.68 17.4 8.9 10.4 772.3 09/01/2009 11:25 40.8 17.5 8.9 10.4 777.6 09/01/2009 11:26 40.68 17.3 8.8 10.4 777.4 09/01/2009 11:27 40.46 17.2 8.8 10.4 770.4 09/01/2009 11:28 40.34 17.3 8.8 10.4 765.2 09/01/2009 11:29 39.96 17.3 8.8 10.3 759.2 Run 8

Page 15 of 16

### CEMS Data

09/01/2009 11:30 39.7 16.8 8.8 10.4 765.9 09/01/2009 11:31 39.32 17.1 8.8 10.4 766.9 09/01/2009 11:32 40.07 17.4 8.9 10.4 769.9 09/01/2009 11:33 40.05 17.3 8.8 10.4 772.8 09/01/2009 11:34 40.45 17.1 8.8 10.4 770.8 09/01/2009 11:35 40.42 17.2 8.8 10.4 763 09/01/2009 11:36 40.44 17.3 8.8 10.4 759.3 09/01/2009 11:37 40.77 17.3 8.8 10.4 767.2 09/01/2009 11:38 40.9 17.1 8.8 10.4 776.6 09/01/2009 11:39 41.05 17.2 8.8 10.4 770.3 09/01/2009 11:40 40.53 17.3 8.8 10.4 751.5 09/01/2009 11:41 40.6 17.2 8.8 10.4 759.8 09/01/2009 11:42 40.56 17.2 8.8 10.4 772.5 09/01/2009 11:43 40.93 17 8.8 10.4 776.8 09/01/2009 11:44 40.72 17.2 8.8 10.4 758.9 09/01/2009 11:45 40.63 17.2 8.8 10.4 762.3 09/01/2009 11:46 40.67 17.3 8.8 10.4 754.6 09/01/2009 11:47 40.2 17.2 8.8 10.4 750.7 09/01/2009 11:48 40.06 17.1 8.8 10.4 750.9 09/01/2009 11:49 40.49 17.1 8.8 10.4 744.8 09/01/2009 11:50 39.97 17.1 8.8 10.4 768.2 09/01/2009 11:51 40.35 17.3 8.8 10.4 776.2 09/01/2009 11:52 40.36 17.2 8.8 10.4 767.8 09/01/2009 11:53 40.37 17.2 8.8 10.3 755.5 09/01/2009 11:54 40.28 17.3 8.8 10.3 752.8 09/01/2009 11:55 39.97 16.9 8.8 10.3 762 09/01/2009 11:56 39.95 16.9 8.8 10.3 766.8 09/01/2009 11:57 40.16 17 8.7 10.3 774.3 09/01/2009 11:58 39.96 17 8.8 10.3 757 40.274706 17.28 8.804 10.38 765.972059 765972.059 704587.301 Average for test da y 40.328035 17.32 8.764 10.37 770.658757

Page 16 of 16

## APPENDIX E

TEST PARTICIPANTS

## TEST PARTICIPANTS

AIR SERVICES GROUP

Scott Given Environmental Technician – Test Team Lead Jorge Varino Environmental Technician Gary Barber Environmental Technician Ryan Newell Environmental Technician Ray McDarby Senior Environmental Technician David A. Smith, QSTI Coordinator – Air Services Group

Process Data Ray McDarby Senior Environmental Technician Fuel Analysis Ray McDarby Senior Environmental Technician Project Quality Objectives & Reporting Ray McDarby Senior Environmental Technician
Test Coordination David A. Smith, QSTI Coordinator, Air Services Group
POLK POWER STATION

Michael Perkins Environmental Coordinator Josh Ellwein Principal Engineer, Air Programs