Polyvinyl Chloride and Copolymers (PVC) Production

MACT Floor, Baseline Emissions, and Emission Reductions Analyses

Heat Exchange Systems

February 7, 2012

Worksheet Name Description 

Survey Data (Form D) Section 114 Survey Data for Heat Exchange Systems

Monitoring Programs - Pivot Monitoring Programs Data Extraction

Monitoring Programs - Summary Summary of Monitoring Programs

Flow Rates - Pivot Flow Rate Data Extraction

Reported Emissions from CTs Reported Emisisons from Cooling Towers - Survey Data Responses

Form C-1-A Data Section 114 Survey Form C-1-A Data Summary

Survey Data Summary Heat Exchange Systems - Survey Data Analysis and Summary

Clarification Data Heat Exchange Systems - Summary of Clarification Data Submitted to EPA

FLOOR Calculation MACT Floor Analysis - Heat Exchange Systems

Baseline, Reductions, Costs COOLING TOWERS - BASELINE EMISSIONS ANALYSIS

Count for PVC HeatExch COOLING TOWERS - Count for PVC HeatExch
CompanyName

Georgia Gulf Corporation

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Georgia Gulf Corporation

Georgia Gulf Corporation

Georgia Gulf Corporation

Georgia Gulf Corporation

Georgia Gulf Corporation

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

CertainTeed Corporation
CertainTeed Corporation

CertainTeed Corporation

CertainTeed Corporation

The Dow Chemical Company

The Dow Chemical Company

Union Carbide Corporation

Union Carbide Corporation

Union Carbide Corporation

Union Carbide Corporation

Union Carbide Corporation

Union Carbide Corporation

Union Carbide Corporation

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP
OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

Westlake Chemical Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

PolyOne Corporation

Westlake Chemical Corporation

Westlake Chemical Corporation

Westlake Chemical Corporation
Westlake Chemical Corporation

Westlake Chemical Corporation

Westlake Chemical Corporation

Westlake Chemical Corporation
FacilityName ProcessUnitID

Georgia Gulf Chemicals Plaquemine Facility P-1

OxyVinyls Pedricktown P-1

OxyVinyls Pedricktown P-1

OxyVinyls Pedricktown P-1

OxyVinyls Pedricktown P-2

OxyVinyls Pedricktown P-2

OxyVinyls Pedricktown P-2

OxyVinyls Pedricktown P-3

OxyVinyls Pedricktown P-3

OxyVinyls Pedricktown P-3

OxyVinyls Pedricktown P-3

OxyVinyls Pedricktown P-4

Formosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation Deleware City P1

Formosa Plastics Corporation Deleware City P-2

Formosa Plastics Corporation Point Comfort - PVC Unit P-1

Formosa Plastics Corporation Point Comfort - PVC Unit P-1

Formosa Plastics Corporation Point Comfort - PVC Unit P-1

Formosa Plastics Corporation, Point Comfort - Specialty Polyvinyl Chloride (SPVC) Unit P-2

Georgia Gulf Chemicals Aberdeen Facility 1

Georgia Gulf Chemicals Aberdeen Facility 1

Georgia Gulf Chemicals Plaquemine Facility P-1

Georgia Gulf Chemicals Plaquemine Facility P-1

Georgia Gulf Chemicals Plaquemine Facility P-1

OxyVinyls Pedricktown P-5

OxyVinyls Pedricktown P-6

OxyVinyls Pedricktown P-6

OxyVinyls Pedricktown P-6

OxyVinyls Pedricktown P-6

OxyVinyls Pedricktown P-6

OxyVinyls Pedricktown P-6

OxyVinyls Pedricktown P-7

Shintech Addis P-1

Shintech Addis P-1

Shintech Addis P-1

Shintech Addis P-1

Shintech Freeport P-1

Shintech Freeport P-1

Shintech Freeport P-1

Shintech Freeport P-1

Shintech Plaquemine P-1

Shintech Plaquemine P-1

Shintech Plaquemine P-1

Shintech Plaquemine P-1

Lake Charles Polymer Plant P-1
Lake Charles Polymer Plant P-1

Lake Charles Polymer Plant P-1

Lake Charles Polymer Plant P-2

Dow Midland - SARAN Resins Vinyl Train

Dow Midland - SARAN Resins Vinyl Train

Union Carbide Texas City P-1, P-2

Union Carbide Texas City P-1, P-3

Union Carbide Texas City P-1, P-2, P-3

Union Carbide Texas City P-2, P-3

Union Carbide Texas City P-2, P-3

Union Carbide Texas City P-2

Union Carbide Texas City P-1

OxyVinyls Deer Park P-1

OxyVinyls Deer Park P-1

OxyVinyls Deer Park P-1

OxyVinyls Deer Park P-1

OxyVinyls Deer Park P-1

OxyVinyls Deer Park P-1

OxyVinyls Deer Park P-2

OxyVinyls Deer Park P-2

OxyVinyls Deer Park P-2

OxyVinyls Deer Park P-2

OxyVinyls Deer Park P-2

OxyVinyls Deer Park P-3

OxyVinyls Deer Park P-4

OxyVinyls Deer Park P-4

OxyVinyls Deer Park P-4

OxyVinyls Deer Park P-4

OxyVinyls Deer Park P-4

OxyVinyls Deer Park P-4

OxyVinyls Deer Park P-4

OxyVinyls Pasadena P1

OxyVinyls Pasadena P1

OxyVinyls Pasadena P1

OxyVinyls Pasadena P1

OxyVinyls Pasadena P3

OxyVinyls Pasadena P4

OxyVinyls Pasadena P5

OxyVinyls Pasadena P6

OxyVinyls Pasadena P7

OxyVinyls Pasadena P8

OxyVinyls Pasadena P9

OxyVinyls Pasadena P3

OxyVinyls Pasadena P4

OxyVinyls Pasadena P5

OxyVinyls Pasadena P6

OxyVinyls Pasadena P7

OxyVinyls Pasadena P8

OxyVinyls Pasadena P9

OxyVinyls Pasadena P3

OxyVinyls Pasadena P4

OxyVinyls Pasadena P5
OxyVinyls Pasadena P6

OxyVinyls Pasadena P7

OxyVinyls Pasadena P8

OxyVinyls Pasadena P9

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P10

OxyVinyls Pasadena P11

OxyVinyls Pasadena P11

OxyVinyls Pasadena P12

OxyVinyls Pasadena P12

PolyOne Henry P-13 Cooling Twr for P-4

PolyOne Henry P-13 Cooling Twr for P-4

PolyOne Henry P-13 Cooling Twr for P-4

PolyOne Henry P-13 Cooling Twr for P-5

PolyOne Henry P-13 Cooling Twr for P-5

PolyOne Henry P-13 Cooling Twr for P-5

PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Henry Chilled H2O - L4

PolyOne Henry P-14 Chilled H2O for P-5

PolyOne Henry P-14 Chilled H2O for P-5

PolyOne Henry P-14 Chilled H2O for P-5

PolyOne Henry P-14 Chillers

PolyOne Pedricktown P-1

Westlake Calvert City P-1

PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Henry P-13 Cooling Twr for P-2

PolyOne Henry P-13 Cooling Twr for P-2

Westlake Calvert City P-1

Westlake Calvert City P-1

Westlake Calvert City P-1
Westlake Calvert City P-1

Westlake Geismar P-1

Westlake Geismar P-1

Westlake Geismar P-1
ProcessEquipID1 ProcessEquipID2 ProcessEquipID3 ProcessEquipID4 ProcessEquipID5

U-166 thru U-173 U-1 thru U-18 U-142 thru U-149

U-100

U-115

U-107

U-200

U-207

U-218

U-309

U-311

U-310

U-303

N/A

PE205A

PE206A PE206C

PE206B

PE301 PE302 PE310

PE303A/B

PE304A/B PE-305A/B

PE309

U-14 U-27 U-28 U-29 U-30

U-60 U-75 U-76 U-77 U-78

U-7 U-24

U-19 U-24

U-3 U-25

U-17 U-43 / U-44 U-45 / U-46 U-47 U-57

U-34 thru 45

U-46 thru 53

U-175

U-176 U-19 + U-20 U-63 + U-64

U-182

U-508

U-600

U-611

U-616

U-610

U-613

U-615

N/A

U-28 U-34A U-34B U-50A U-50B

U-2 U-27A-D U-38A U-38B U-49

U-35A U-35B U-36A U-36B

U-60

U-43

U-39 U-48 U-49

U-21A thru D U-23A thru D

U-14A thru F U-16 U-20A thru D U-24A thru D

U-25 U-30 U-46A thru B U-51 U-54

U-24A thru B U-34 U-45 U-47 U-53

U-31 U-32

U-56

U-5a U-5b U-5c U-5d U-5e
U-10a U-10b U-10c

U-10d

U-16a U-16b U-16c U-16d

CTW-1 R-302 Jacket R-303 Jacket R-304 Jacket R-305 Jacket

CTW-1 E-511 E-512 E-521 E-522

U-1 U-5 U-12 U-16 U-20

U-3 U-7 U-9 U-10 U-11

U-14 U-24 U-44 U-57 U-58

U-20 U-24 U-57 U-58 U-60

U-28 U-47 U-34 C-3

U-34

U-14

U-102

U-135

U-110

U-111

U-118

U-131

U-202

U-231

U-210

U-214

U-131

U-315

U-419

U-403

U-404

U-410

U-411

U-414

U-413

U119

U120

U121

U122

U300

U400

U500

U600

U700

U800

U900

U304

U404

504

U604

U704

U804

U904

U308

U408

U508
U608

U708

U808

U908

U1006

U1041

U1046

U1051

U1027

U1030

U1028

U1031

U1035

U1034

U1033

U1037

U1103

U1104

U1203

U1219

Poly 1 Jacket Poly 2 Jacket Poly 3 Jacket Poly 4 Jacket Poly 1 Baffle

Poly 4 Baffle Upper Recovery Lower Recovery Column 3 Cond Lean Oil Cooler

Seal H2O Heat Xch

Poly 5 Jacket Poly 6 Jacket Poly 7 Jacket Poly 8 Jacket Poly 9 Jacket

Poly 12 Jacket Poly 5 Baffle Poly 6 Baffle Poly 7 Baffle Poly 8 Baffle

Poly 11 Baffle Poly 12 Baffle Column 2

Poly 21 Jacket Poly 22 Jacket Poly 23 Jacket Poly 24 Jacket Poly 25 Jacket

Poly 28 Jacket Poly 29 Jacket Poly 30 Jacket Poly 31 Jacket Poly 32 Jacket

Poly 35 Jacket Poly 36 Jacket Poly 21 Condenser Poly 22 Condenser Poly 23 Condenser

Poly 26 Condenser Poly 27 Condenser Poly 28 Condenser Poly 29 Condenser Poly 30 Condenser

Poly 33 Condenser Poly 34 Condenser Poly 35 Condenser Poly 36 Condenser L1 Slurry Cooler

Poly 37 Jacket Poly 38 Jacket Poly 39 Jacket Poly 40 Jacket Poly 37 Condenser

Poly 40 Condenser Premix Jacket L2 Slurry Cooler

Poly 1 Jacket Poly 2 Jacket Poly 3 Jacket Poly 4 Jacket Poly 1 Baffle

Poly 4 Baffle Upper Recovery Lower Recovery Column 3 Cond Lean Oil Cooler

P-14 Chilled H2O for P-4

Poly 5 Jacket Poly 6 Jacket Poly 7 Jacket Poly 8 Jacket Poly 9 Jacket

Poly 12 Jacket Poly 5 Baffle Poly 6 Baffle Poly 7 Baffle Poly 8 Baffle

Poly 11 Baffle Poly 12 Baffle Column 2

Chiller Unit 1 Chiller Unit 2

U-18

U-8 U-9 U-11 U-12 U-14

Poly 21 Jacket Poly 22 Jacket Poly 23 Jacket Poly 24 Jacket Poly 25 Jacket

Poly 28 Jacket Poly 29 Jacket Poly 30 Jacket Poly 31 Jacket Poly 32 Jacket

Poly 35 Jacket Poly 36 Jacket Poly 21 Condenser Poly 22 Condenser Poly 23 Condenser

Poly 26 Condenser Poly 27 Condenser Poly 28 Condenser Poly 29 Condenser Poly 30 Condenser

Poly 33 Condenser Poly 34 Condenser Poly 35 Condenser Poly 36 Condenser L1 Slurry Cooler

Poly 37 Jacket Poly 38 Jacket Poly 39 Jacket Poly 40 Jacket Poly 37 Condenser

Poly 40 Condenser Premix Jacket L2 Slurry Cooler

U-17 U-16 U-89

U-22 U-26 U-89 U-34

U-30 U-89
U-40 U-42 U-45 U-89

U-3 U-20 U-23 U-24 U-26

U-31

U-13
ProcessEquipID6 ProcessEquipID7 CoolingWaterSidePressure_Kpa

690

370

275

275

370

0

275

415

415

415

415

480

480

480

480

653

480

515

U-15 U-11 60

U-79 60

345

345

620

U-58 584

790

790

345

414

620

400

0

410

410

200

1400

210

U-55 U-58 430

U-51 U-57 400

305

240

240

450

380

330

423

424

353

267

U-5f U-5g 551.58056
551.58056

551.58056

551.58056

E-501 E-502 450 to 500

E-112 E-702 450 to 500

U-17 241

U-13 U-59 240

240

U-44 U47 240

240

240

240

310

310

350

350

365

Unknown

310

310

350

365

Unknown

430

101.4

690

310

atmospheric

atmospheric

310

310

420

340

340

340

180

180

180

330

330

330

565

550

550

480

480

480

825

825

620

450

450
620

900

620

760

340

480

480

480

520

520

4507

480

1480

1330700

385

650

Poly 2 Baffle Poly 3 Baffle 618

VGA Reflux WWS Condenser 618

618

Poly 10 Jacket Poly 11 Jacket 618

Poly 9 Baffle Poly 10 Baffle 618

618

Poly 26 Jacket Poly 27 Jacket 412

Poly 33 Jacket Poly 34 Jacket 412

Poly 24 Condenser Poly 25 Condenser 412

Poly 31 Condenser Poly 32 Condenser 412

412

Poly 38 Condenser Poly 39 Condenser 412

412

Poly 2 Baffle Poly 3 Baffle 412

VGA Reflux WWS Condenser 412

412

Poly 10 Jacket Poly 11 Jacket 412

Poly 9 Baffle Poly 10 Baffle 412

412

412

700

U-15 U-89 586

Poly 26 Jacket Poly 27 Jacket 618

Poly 33 Jacket Poly 34 Jacket 618

Poly 24 Condenser Poly 25 Condenser 618

Poly 31 Condenser Poly 32 Condenser 618

618

Poly 38 Condenser Poly 39 Condenser 618

618

586

586

586
586

U-30 35

200

330
ProcessSidePressure_Kpa HeatExchangersCnt CoolingWaterFlowRateAvg_Gpm

930 26 17000

840 3 1200

275 2 220

0 1 106

840 3 1200

275 1 26000

275 2 220

0 1 30

0 3 15

0 3 20

0 4 5

116 12 125

122 12 250

127 12 250

580 12

446 12

411 12 1500

585 12 50

21 4000

15

0 7 46200

345 4 46200

1034 10 66300

630 7 100

930 12 1000

450 9 1000

414 47 40000

827 10 22300

0 1181

80 5 50

0 4 13333

140 1 70

35 1 150

140 1 100

100 1 15

200 1 100

260 7 449

630 10 348

380 4 208

205 1 45

240 1 60

400 3 340

380 8 200

340 20 360

292 6 433

543 6 162

222 2 280

212 1 33

806.686569 7 10000
379.211635

3 100

468.8434761 100

806.6865694 5000

0 to 6906 2400

0 to 6906 2400

117 29 500 2 15 300

344 45 900

34 2800 200 2 3 25

342 50

344.5 15 300

4151 Unknown

8271 2200

3501 140

3501 130

3501 Unknown

Unknown1 Unknown

4151 Unknown

8271 2200

3501 140

3501 Unknown

Unknown1 Unknown

3601 75

12414 Unknown

1001 Unknown

Unknown2 Unknown

atmospheric1 8400

atmospheric1 1200

3801 1600

Unknown4 8400

01 44

014

014

014

8602 1265

8602 1265

8602 1265

8602 655

8602 655

8602 655

8602 910

8601 240

8601 240

8601 175

11001 215

11001 215

Process side pressure (kPa)1 260

Process side pressure (kPa)1 260

01 2100

01 1350

01 1350
0

1 2100

01 1500

01 2100

01 2600

5752 200

01 125

01 125

1731 125

5701 1625

5701 1625

5701 1870

5202 1870

14801 250

25851 1870

71 1870

13301 1870

03 9000

02 11600

3801 240

5203 750

1101 15 3000

1101 15 3000

1101 15 3000

1273 17 3000

1273 17 3000

1273 17 3000

722 33 2500

722 33 2500

722 33 2500

722 33 2500

722 33 2500

928 10 2500

928 10 2500

1101 15 2500

1101 15 2500

1101 15 2500

1273 17 2500

1273 17 2500

1273 17 2500

3772 2500

12251 100

08 100

722 33 3000

722 33 3000

722 33 3000

722 33 3000

722 33 3000

928 10 3000

928 10 3000

896 16 20000 0 3 500

8634 200
689 10 2000

480 15 12500

1303 1500

02 650
IsHeatExchangeSystemRegulated HeatExchangeSystemRegulations

No

No

No

No

No

No

No

No

No

No

No

Yes LAC 33:III.1311.C

Yes LAC 33:III.1311.C

Yes LAC 33:III.1311.C

Yes LAC 33:III.1311.C

Yes LAC 33:III.1311.C

Yes LAC 33:III.1311.C

Yes LAC 33:III.1311.C

No

No

Yes State Permit

Yes State Permit

No

Yes State Permit

No

No

Yes 40CFR61+63

Yes 40CFR61+63

No

No

No

No

No

No

No

No

Yes 40 CFR 63.104

No

Yes 40 CFR 61

Yes 40 CFR 61

No

No

No

No

Yes

No

No

Yes

No
No

No

No

Yes Subpart FFFF

Yes Subpart FFFF

No

No

No

No

No

No

No

No

No

Yes 30 TAC 115 Sub. D

Yes 30 TAC 115 Sub. D

Yes 30 TAC 115 Sub. D

No

No

No

Yes 30 TAC 115 Sub. D

Yes 30 TAC 115 Sub. D

No

Yes 30 TAC 115 Sub. D

No

No

No

No

No

No

No

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116
Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116

Yes 40 CFR 61, Subpart V; 30 TAC 116

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No

No
No

Yes LAC 13; LAC 51

No

No
HeatExchangeSystemType DoesSystemProcessFluidsContainingHAPOrVOC HasInterveningFluid

Recirculating Yes No

recirulating Yes No

once-through Yes No

once-through Yes No

recirulating Yes No

Once-Through No No

once-through Yes No

recirculating Yes No

recirculating Yes No

recirculating Yes No

recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes Yes

Recirculating Yes Yes

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Both Yes No

Recirculating Yes No

recirculating Yes No

Recirculating CT Yes No

Recirculating CT Yes No

Recirculating

recirculation Yes No

recirculating Yes No

recirculating Yes No

recirculation Yes No

once through Yes No

once through No No

once through No No

Recirculating Yes No

N/A Yes No

N/A Yes No

N/A Yes No

N/A No No

N/A No No

N/A No No

RECIRCULATING No No

Recirculating Yes No

N/A Yes No

N/A Yes No

N/A Yes No

Recirculating Yes No
Recirculating Yes Yes

Recirculating Yes Yes

Recirculating Yes No R Yes No R Yes No

Recirculating brine Yes No

Recirculating brine No No

Cooling Tower Yes No

Cooling Tower Yes No

Recirculating brine No No

Cooling Tower Yes No

Recirc brine Yes No

Recirculating Yes No

recirculating Yes No

once-through Yes No

once-through Yes No

recirculating Yes No

once-through Yes No

Recirculating Yes No

recirculating Yes No

once-through Yes No

recirculating Yes No

once-through Yes No

once-through Yes No

Recirculating No No

once-through Yes No

recirculating Yes No

Recirculating Yes No

recirculating Yes No

Recirculating No No

Recirculating No No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

Recirc Yes No

once through Yes No

once through Yes No

once through Yes No

once through Yes No

once through Yes No

once through Yes No

once through Yes No

Recirc No Yes

Recirc No Yes

Recirc No Yes
Recirc No Yes

Recirc No Yes

Recirc No Yes

Recirc No Yes

Recirc Yes No

recirc Yes No

recirc Yes No

recirc Yes No

recirc Yes No

recirc Yes No

recirc Yes No

recirc Yes No

once through Yes No

recirc Yes No

recirc Yes No

recirc Yes No

recirc Yes No

recirc Yes No

once through Yes No

once through No No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculation Yes No

RECIRCULATING Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

Recirculating Yes No

RECIRCULATING Yes No

RECIRCULATING Yes No

RECIRCULATING Yes No
RECIRCULATING Yes No

Recirculating Yes No

Recirculating Yes Yes

Recirculating Yes Yes
DoesInterveningFluidContainHAPOrVOC TotalVOC_PctByWeight TotalVOCNote HAP1

No

No
No

No

No

No

Unknown Cumene

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Methanol

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

Unknown Vinyl chloride

N/A Unknown Cumene

N/A Unknown Cumene

N/A Unknown Cumene

N/A Unknown Cumene

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde
No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

No Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

N/A

N/A Unknown Acetaldehyde

N/A

N/A

N/A Unknown Acetaldehyde

N/A Unknown Acetaldehyde

No Unknown Acetaldehyde

N/A Unknown Acetaldehyde
No

Yes 25 Ethylene glycol

No
HAP1_PctByWeight HAP1Note HAP2 HAP2_PctByWeight HAP2Note HAP3
Unknown Methanol Unknown

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown Methanol Unknown Acetaldehyde

Unknown

Unknown

Unknown

Unknown

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene
Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene
25
HAP3_PctByWeight HAP3Note HAP4 HAP4_PctByWeight HAP4Note HAP5
Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown

Unknown

Unknown

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown AcetophenoneUnknown Cumene

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride
Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

Unknown FormaldehydeUnknown Vinyl chloride

HAP5_PctByWeight HAP5Note IsMonitoredForHAPOrVOCInCoolingWater

No

Yes

Yes

Yes

No

Yes

No

No

No

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

No

No

No

Yes

Yes

Yes

No

No
No

No

No

Yes

Yes

No

No

No

No

No

No

No

No

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown No

No

Yes

Unknown No

Unknown No

Unknown No

Unknown Yes

Unknown Yes

Unknown Yes

No

No

Yes

Yes

Yes

Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes
Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Yes

Unknown Yes

Yes

Yes

Unknown Yes

Unknown Yes

Unknown Yes

Unknown Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

Yes

No

Yes

Yes

Yes

Yes

Yes

Yes

Yes

No

No

No
No

No

No
ProceduresToIdentifyLeaks MonitoringSamplingFreq

High readings identified by the VCM Area Monitoring System requires follow up investigation by Water is not sampled / VCM Area Monitoring Sy Operator with hand held meterste

GC monitoring of cooling tower airspace every 15 minutes

Residual VCM is monitored in the outlet stream of the stripped slurry (hot side) every 8 hours

Residual VCM is monitored in the outlet stream of the stripped slurry (hot side) every 8 hours

GC monitoring of cooling tower airspace every 15 minutes

Residual VCM is monitored in the outlet stream of the stripped slurry (hot side) every 8 hours

Residual VCM is monitored in the outlet stream of the stripped slurry (hot side) every 8 hours

HE's are monitored only when unusual conditions are noted. N/A

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly

Water is sampled weekly. If VOC detected than individual equipment is sampled. Weekly

Sampling of the cooling tower for VCM/EDC/NMHC Twice per day

Sampling of the cooling tower for VCM/EDC/NMHC Twice per day

Sampling of the chill water tanks for VCM Twice per week

Sampling of cooling tower for VCM and NMHC Weekly

Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. Quarterly

Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. Quarterly

Samples caught and analyzed Weekly

Samples caught and analyzed Weekly

Samples caught and analyzed 4 times daily

Gas Chromatograph sample point every 15 minutes

Gas Chromatograph sample point every 15 minutes

Gas Chromatograph sample point every 15 minutes

Gas Chromatograph sample point every 15 minutes

None

LDAR and NESHAP Quarterly Monitoring Quarterly

LDAR & NESHAP Quarterly Monitoring Quarterly

LDAR Quarterly Monitoring Quarterly

LDAR Quarterly Monitoring Quarterly

LDAR and NESHAP Quarterly Monitoring daily leak patrol 

LDAR and NESHAP Quarterly Monitoring daily leak patrol 

LDAR and NESHAP Quarterly Monitoring daily leak patrol 

LDAR and NESHAP Quarterly Monitoring daily leak patrol 

LDAR and NESHAP Quarterly Monitoring Quarterly

LDAR and NESHAP Quarterly Monitoring Quarterly

LDAR and NESHAP Quarterly Monitoring Quarterly

LDAR and NESHAP Quarterly Monitoring Quarterly

Not required - not a major source of HAP emissions N/A
Not required - not a major source of HAP emissions N/A

Not required - not a major source of HAP emissions N/A

Not required - not a major source of HAP emissions N/A

Quarterly

Quarterly

Brine would leak into the process and be picked up by process monitors Continuous analyzers and level monitoring detect b

Brine leaks detected by process analyzers, process levels and brine levels Continuous analyzers and level monitoring detect b

Vessel testing and leakage into the process when depressurized 5 year pressure test and inspection.

Vessel testing and Cycle Water leakage into process 5 year pressure test and inspection.

Brine leaks detected by process analyzers, process levels and brine levels Continuous analyzers and level monitoring detect b

Vessel testing and Cycle Water leakage into process 5 year pressure test and inspection.

Vessel testing and Brine leakage into process, when vessel depressurized 5 year pressure test/inspection and level during wa

Process Side flow is not continuous If there were a failure of the exchanger, cooling water would back intothe process side and N/A

Weekly testing of the chilled water to detect the presence of VCM. In addition, a GC/MS anlay Weekly / Continuously zer is positioned at the vent of th

Residual VCM is monitored in the outlet stream of the stripped slurry (hot side) every 8 hours

Residual VCM is monitored in the outlet stream of the stripped slurry (hot side) every 8 hours

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly zers in the area would dete

Periodic maintenance inspection. Although the centrate water may contain levels of HAPS, this sy None stem does not contain VCM 

Process Side flow is not conintuous. If there were a failure of the exchanger, cooling water would back intothe process side anN/A

Weekly testing of the chilled water to detect the presence of VCM. In addition, a GC/MS anlay Weekly / Continuously zer is positioned at the vent of th

Residual VCM is monitored in the outlet stream of the stripped slurry (hot side) every 8 hours

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly zers in the area would dete

Periodic maintenance inspection. Although the centrate water may contain levels of HAPS, this sy None stem does not contain VCM 

Weekly Sample of WW Stripper discharge. In addition, area GC monitors would detect fugitive VCM if present. Weekly

Although the centrate water may contain levels of HAPS, this system does not contain VCM and is not monitored.

The chilled water is sampled and tested for VCM; Chill Water storage tank has a GC/MS sample point running continuously Weekly wh

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly zers in the area would dete

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly zers in the area would dete

None N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A

The chilled water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The chilled water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The chilled water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The stripped slurry is sampled. The sample is analyzed for residual VCM Three times per day

The stripped slurry is sampled. The sample is analyzed for residual VCM Three times per day

The stripped slurry is sampled. The sample is analyzed for residual VCM Three times per day

The stripped slurry is sampled. The sample is analyzed for residual VCM Three times per day

The stripped slurry is sampled. The sample is analyzed for residual VCM Three times per day

The stripped slurry is sampled. The sample is analyzed for residual VCM Three times per day

The stripped slurry is sampled. The sample is analyzed for residual VCM Three times per day

N/A N/A

N/A N/A

N/A N/A
N/A N/A

N/A N/A

N/A N/A

N/A N/A

sample only when needed

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

DCS Continuous

DCS Continuous

DCS Continuous

DCS Continuous

Sample Weekly

Refrigeration machine shutdown N/A

Refrigeration machine shutdown N/A

Refrigeration machine shutdown N/A

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly

The stripped waste water sampled. The sample is analyzed for residual VCMWeekly

N/A N/A

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Pm's by contractor. Check for leaks and amount of Freon 134a lost. Refill and record amount Quarterly

Routine sampling of System Once per week

None

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

Water is sampled for residual VCM per Method 107. If VCM is detected we sy1/ shift or 2 /day tematically pressure check and sample around e

None

None

None
None

None

None

None
TestMethod1 TestMethod2 TestMethod3 TestMethod4

 not sampled / VCM Area Monitoring System 

Real-time Gas Chromotography

EPA-107

EPA-107

Real-time Gas Chromotography

EPA-107

EPA-107

Method 624

Method 624

Method 624

Method 624

Method 624

Method 624

Method 624

106

EPA Method 601

EPA Method 601

EPA Method 601

EPA Method 601

EPA Method 107

EPA Method 107

Lab Procedure # PPVC 27, "Residual Vinyl Chloride using Perkin Elmer HS40B"

Lab Procedure # PPVC 27, "Residual Vinyl Chloride using Perkin Elmer HS40B"

Lab Procedure # PPVC 27, "Residual Vinyl Chloride using Perkin Elmer HS40B"

Real Time Gas Chromatography

Real Time Gas Chromatography

Real Time Gas Chromatography

Real Time Gas Chromatography

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

N/A
N/A

N/A

N/A

415.1

415.1

Near Infrared level measurement

Near Infrared Level measurement

N/A

N/A

Near Infrared Level measurement

N/A

N/A

N/A

EPA-107

EPA-107

EPA-107

EPA-107

None

N/A

EPA-107

EPA-107

EPA-107

None

EPA-107

n VCM and is not monitored.

EPA-107

EPA-107

EPA-107

N/A

N/A

N/A

N/A

N/A

EPA107 (Weekly) Method 624 (Monthly)

EPA107 (Weekly) Method 624 (Monthly)

EPA107 (Weekly) Method 624 (Monthly)

EPA107 (Weekly) Method 624 (Monthly)

EPA107 (Weekly) Method 624 (Monthly)

EPA107 (Weekly) Method 624 (Monthly)

EPA107 (Weekly) Method 624 (Monthly)

EPA107

EPA107

EPA107

EPA107

EPA107

EPA107

EPA107

N/A

N/A

N/A
N/A

N/A

N/A

N/A

titration

EPA107 Method 624

EPA107 Method 624

EPA107 Method 624

N/A

N/A

N/A

N/A

EPA107

N/A

N/A

N/A

EPA107 Method 624

EPA107 Method 624

EPA107

N/A

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Gas Chromotograph

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

Method 107

LocationOfCollectedSamples AreSurrogateIndicatorsUsedToDetectLeaks

Yes

Stationary sampling point above hot water basin No

discharge of stripped slurry exchanger No

discharge of stripped slurry exchanger No

Stationary sampling point above hot water basin No

discharge of stripped slurry exchanger No

discharge of stripped slurry exchanger No

Chilled water storage tank owned and operated by PolyOne. No

No

No

No

Inlet and outlet of cooling tower No

Inlet and outlet of cooling tower No

Inlet and outlet of cooling tower No

Inlet and outlet of cooling tower No

Inlet and outlet of cooling tower No

Inlet and outlet of cooling tower No

Inlet and outlet of cooling tower No

Water utility station

Cooling Tower No

Cooling Tower No

Chill water tanks No

Cooling Tower No

Exchanger outlet No

Exchanger outlet No

Cooling Tower Outlet No

Cooling Tower Outlet No

Cooling Tower Outlet No

air space above hot water basin No

air space above hot water basin No

air space above hot water basin No

air space above hot water basin No

No

No

No

Cooling Tower entrance and exit No

Connectors No

Connectors No

Connectors No

Connectors No

Connectors No

Connectors No

Connectors No

N/A No
N/A No

N/A No

N/A No

CTW inlet and outlet No

CTW inlet and outlet No

Inline optic monitor, no external samples No

No, Inprocess anayzers and level measurements No

N/A No

N/A No

No, Inprocess anayzers and level measurements No

N/A No

N/A No

No No

Chill water pump discharge No

discharge of stripper economizer No

discharge of stripper economizer No

Cooling Tower Basin No

N/A No

N/A No

Chill water pump discharge No

discharge of stripper economizer No

Cooling Tower Basin No

N/A No

Discharge of Stripper to process sewer No

Chill water pump discharge No

Cooling Tower Basin No

Cooling Tower pump discharge No

N/A No

N/A No

N/A No

N/A No

N/A No

N/A No

Pump discharge. No

Pump discharge. No

Pump discharge. No

Pump discharge. No

Pump discharge. No

Pump discharge. No

Pump discharge. No

U308 & U408 outlet No

U308 & U408 outlet No

U508 outlet No

U608 & U708 outlet No

U608 & U708 outlet No

U908 & U908 outlet No

U908 & U908 outlet No

N/A No

N/A No

N/A No
N/A No

N/A No

N/A No

N/A No

pump discharge No

Pump discharge. No

Pump discharge. No

Pump discharge. No

N/A Yes

N/A Yes

N/A Yes

N/A Yes

Pump discharge. No

N/A Yes

N/A Yes

N/A Yes

Pump discharge No

Pump discharge No

Pump discharge No

N/A No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

From sample bleed on outlet of chilled water pumps No

No

Refrigeration Water Collection Tank No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

From Cooling tower as water falls into basin. No

SurrogateIndicatorsUsed ValueToIndicateALeak

VCM Area Monitoring Follow Up Investigation by Operator with Hand Held Meter

N/A N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A

>5 ppb/>5 ppb/>30 ppb

>5 ppb/>5 ppb/>30 ppb

>5 ppb

< 50 ppb

N/A
N/A

N/A

N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A

N/A N/A
Feed Rate Being reduced by controller

Feed Rate Being reduced by controller

FeedRate Being reduced by controller

FeedRate Being reduced by controller

Shutdown Down

Shutdown Down

Shutdown Down
Monitoring Programs

Count of ValueToIndicateALeak

CompanyName FacilityName IsHeatExchangeSystemRegulated HeatExchangeSystemRegulations HeatExchangeSystemType IsMonitoredForHAPOrVOCInCoolingWaterProceduresToIdentifyLeaks MonitoringSamplingFreq TestMethod1 TestMethod2 TestMethod3 TestMethod4 LocationOfCollectedSamples AreSurrogateIndicatorsUsedToDetectLeaksSurrogateIndicatorsUsed ValueToIndicateALeak Total

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge Yes LAC 33:III.1311.C Recirculating Yes The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentration of specific HAPs in the cooling water. Quarterly Method 624 (blank) (blank) (blank) Inlet and outlet of cooling tower No N/A N/A 7

Formosa Plastics Corporation Point Comfort - PVC Unit Yes State Permit Recirculating Yes Sampling of the cooling tower for VCM/EDC/NMHC Twice per day EPA Method 601 (blank) (blank) (blank) Cooling Tower No (blank) >5 ppb/>5 ppb/>30 ppb 2

Formosa Plastics Corporation, Point Comfort - Specialty Polyvinyl Chloride (SPVC) Unit Yes State Permit Both Yes Sampling of cooling tower for VCM and NMHC Weekly EPA Method 601 (blank) (blank) (blank) Cooling Tower No (blank) < 50 ppb 1

Georgia Gulf Corporation Georgia Gulf Chemicals Plaquemine Facility Yes 40CFR61+63 Recirculating CT Yes Samples caught and analyzed Weekly Lab Procedure # PPVC 27, "Residual Vinyl Chloride using Perkin Elmer HS40B" (blank) (blank) (blank) Cooling Tower Outlet No (blank) (blank)

OxyVinyls, LP OxyVinyls Deer Park Yes 30 TAC 115 Sub. D Recirculating Yes Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlayzers in the area would detect fugitive VCM. Monthly EPA-107 (blank) (blank) (blank) Cooling Tower Basin No (blank) (blank)

(blank) Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlayzers in the area would detect fugitive VCM. Monthly EPA-107 (blank) (blank) (blank) Cooling Tower Basin No (blank) (blank)

OxyVinyls Pasadena Yes 40 CFR 61, Subpart F; 40 CFR 61, Subpart V; 30 TAC 116Recirc Yes The chilled water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly) Method 624 (Monthly)(blank) (blank) Pump discharge. No (blank) (blank)

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 Method 624 (blank) (blank) Pump discharge. No (blank) (blank)

EPA107 (Weekly) Method 624 (Monthly)(blank) (blank) Pump discharge. No (blank) (blank)

40 CFR 61, Subpart V; 30 TAC 116 Recirc Yes DCS Continuous N/A (blank) (blank) (blank) N/A Yes Feed Rate Being reduced by controller 2

FeedRate Being reduced by controller 2

N/A N/A N/A (blank) (blank) (blank) N/A No N/A N/A 4

(blank) (blank)

Refrigeration machine shutdown N/A N/A (blank) (blank) (blank) N/A Yes Shutdown Down 3

sample only when needed titration (blank) (blank) (blank) pump discharge No (blank) (blank)

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 Method 624 (blank) (blank) pump discharge No (blank) (blank)

Shintech, Inc. Corporate Office Shintech Addis Yes 40 CFR 63.104 Recirculating Yes LDAR and NESHAP Quarterly Monitoring Quarterly Method 107 (blank) (blank) (blank) Cooling Tower entrance and exitNo (blank) (blank)

Shintech Plaquemine Yes (blank) Recirculating Yes LDAR and NESHAP Quarterly Monitoring Quarterly Method 107 (blank) (blank) (blank) Connectors No (blank) (blank)

The Dow Chemical Company Dow Midland - SARAN Resins Yes Subpart FFFF R Yes (blank) Quarterly 415.1 (blank) (blank) (blank) CTW inlet and outlet No N/A N/A 2

Westlake Chemical Corporation Westlake Geismar Yes LAC 13; LAC 51 Recirculating (blank) None (blank) (blank) (blank) (blank) (blank) (blank) (blank) (blank) (blank)

Grand Total 23
Summary of Monitoring Programs

CompanyName FacilityName IsHeatExchangeSystem

Regulated

HeatExchangeSystemRe

gulations

HeatExchangeSystemTy

pe

IsMonitoredForHAPOrV

OCInCoolingWater

ProceduresToIdentifyLe

aks

MonitoringSamplingFreq TestMethod1 TestMethod2 TestMethod3 TestMethod4 LocationOfCollectedSa

mples

AreSurrogateIndicatorsU

sedToDetectLeaks

SurrogateIndicatorsUse

d

ValueToIndicateALeak

Formosa Baton Rouge Yes LAC 33:III.1311.C Recirculating Yes The cooling tower water 

inlet and outlet was 

sampled quarterly in 2008 

and tested using Method 

624 to determine 

concentration of specific 

HAPs in the cooling water. 

Quarterly Method 624 Inlet and outlet of cooling 

tower

No N/A N/A

Formosa Point Comfort - PVC Unit Yes State Permit Recirculating Yes Sampling of the cooling 

tower for 

Twice per day EPA Method 601 Cooling Tower No >5 ppb/>5 ppb/>30 ppb

Formosa Point Comfort - Specialty 

Polyvinyl Chloride (SPVC) 

Unit

Yes State Permit Both Yes Sampling of cooling tower 

for VCM and NMHC

Weekly EPA Method 601 Cooling Tower No < 50 ppb

Georgia Gulf Plaquemine Yes 40CFR61+63 Recirculating CT Yes Samples caught and 

analyzed

Weekly Lab Procedure # PPVC 

27, "Residual Vinyl 

Chloride using Perkin 

Cooling Tower Outlet No

OxyVinyls Deer Park Yes 30 TAC 115 Sub. D Recirculating Yes Monthly testing of the 

cooling tower water to 

detect the presence of 

VCM. In addition, GC/MS 

anlayzers in the area would 

detect fugitive VCM.

Monthly EPA-107 Cooling Tower Basin No

OxyVinyls Deer Park Yes 31 TAC 115 Sub. D Recirculating Monthly testing of the 

cooling tower water to 

detect the presence of 

VCM. In addition, GC/MS 

anlayzers in the area would 

detect fugitive VCM.

Monthly EPA-107 Cooling Tower Basin No

OxyVinyls Pasadena Yes 40 CFR 61, Subpart F; 40 

CFR 61, Subpart V; 30 

TAC 116

Recirc Yes The chilled water is 

sampled. The sample is 

analyzed for VCM.

Weekly & Monthly EPA107 (Weekly) Method 624 (Monthly) Pump discharge. No

OxyVinyls Pasadena Yes 40 CFR 61, Subpart F; 40 

CFR 61, Subpart V; 30 

TAC 116

Recirc Yes The cooling water is 

sampled. The sample is 

analyzed for VCM.

Weekly & Monthly EPA107 Method 624 Pump discharge. No

OxyVinyls Pasadena Yes 40 CFR 61, Subpart F; 40 

CFR 61, Subpart V; 30 

TAC 116

Recirc Yes The cooling water is 

sampled. The sample is 

analyzed for VCM.

Weekly & Monthly EPA107 (Weekly) Method 624 (Monthly) Pump discharge. No

OxyVinyls Pasadena Yes 40 CFR 61, Subpart V; 30 

TAC 116

Recirc Yes DCS Continuous N/A N/A Yes Feed Rate Being reduced by 

TAC 116 controller

OxyVinyls Pasadena Yes 40 CFR 61, Subpart V; 30 

TAC 116

Recirc Yes DCS Continuous N/A N/A Yes FeedRate Being reduced by 

controller

OxyVinyls Pasadena Yes 40 CFR 61, Subpart V; 30 

TAC 116

Recirc Yes N/A N/A N/A N/A No N/A N/A

OxyVinyls Pasadena Yes 40 CFR 61, Subpart V; 30 

TAC 116

Recirc Yes N/A N/A N/A N/A No

OxyVinyls Pasadena Yes 40 CFR 61, Subpart V; 30 

TAC 116

Recirc Yes Refrigeration machine 

shutdown

N/A N/A N/A Yes Shutdown Down

OxyVinyls Pasadena Yes 40 CFR 61, Subpart V; 30 

TAC 116

Recirc Yes sample only when needed titration pump discharge No

OxyVinyls Pasadena Yes 40 CFR 61, Subpart V; 30 

TAC 116

Recirc Yes The cooling water is 

sampled. The sample is 

analyzed for VCM.

Weekly & Monthly EPA107 Method 624 pump discharge No

Shintech Addis Yes 40 CFR 63.104 Recirculating Yes LDAR and NESHAP 

Quarterly Monitoring

Quarterly Method 107 Cooling Tower entrance 

and exit

No

Shintech Plaquemine Yes Recirculating Yes LDAR and NESHAP 

Quarterly Monitoring

Quarterly Method 107 Connectors No

Dow Midland Yes Subpart FFFF R Yes Quarterly 415.1 CTW inlet and outlet No N/A N/A

Westlake Geismar Yes LAC 13; LAC 51 Recirculating None
Cooling Water Flow Rates

Sum of CoolingWaterFlowRateAvg_Gpm

CompanyName FacilityName ProcessUnitID HeatExchangeSystemType ProcessEquipID1 Total

CertainTeed Corporation Lake Charles Polymer Plant P-1 Recirculating U-10a 100

U-10d 100

U-5a ####

P-2 Recirculating U-16a 5000

Formosa Plastics Corporation USA Formosa Plastics Corporation Baton Rouge P-1 Recirculating PE205A 125

PE206A 250

PE206B 250

PE301

PE303A/B

PE304A/B 1500

PE309 50

Formosa Plastics Corporation Deleware City P1 Recirculating U-14 4000

P-2 Recirculating U-60

Formosa Plastics Corporation Point Comfort - PVC Unit P-1 Recirculating U-19 ####

U-3 ####

U-7 ####

Georgia Gulf Corporation Georgia Gulf Chemicals Aberdeen Facility 1 Recirculating U-34 thru 45 1000

U-46 thru 53 1000

Georgia Gulf Chemicals Plaquemine Facility P-1 Recirculating U-166 thru U-173 ####

U-182 1181

Recirculating CT U-175 ####

U-176 ####

OxyVinyls, LP OxyVinyls Deer Park P-1 Recirculating U-102 0

U-118 0

U-135 2200

P-2 Recirculating U-202 0

U-214 0

U-231 2200

P-4 Recirculating U-404 0

U-410 8400

U-411 1200

U-413 8400

U-414 1600

U-419 0

OxyVinyls Pasadena P1 Recirc U119 44

U120 4

U121 4

U122 4

P10 Recirc U1006 200

U1027 1625

U1028 1870

U1030 1625

U1031 1870

U1033 1870

U1034 1870

U1037 1870

U1041 125

U1046 125

U1051 125

P11 Recirc U1103 9000

U1104 ####

P3 Recirc U300 1265

U308 2100

P4 Recirc U400 1265

U408 1350

P5 Recirc U500 1265

U508 1350

P5 Recirc U500 1265

U508 1350

P6 Recirc U600 655

U608 2100

P7 Recirc U700 655

U708 1500

P8 Recirc U800 655

U808 2100

P9 Recirc U900 910

U908 2600

OxyVinyls Pedricktown P-1 recirulating U-100 1200

P-2 recirulating U-200 1200

P-3 Recirculating U-303 5

U-309 30

U-310 20

U-311 15

P-5 recirculation U-508 50

P-6 Recirculating U-600 ####

U-611 70

recirculation U-616 150

PolyOne Corporation PolyOne Henry Chilled H2O - L4 Recirculating P-14 Chilled H2O for P-42500

P-13 Cooling Twr for P-1Recirculating Poly 21 Jacket 3000

Poly 26 Condenser 3000

Poly 28 Jacket 3000

Poly 33 Condenser 3000

Poly 35 Jacket 3000

P-13 Cooling Twr for P-2Recirculating Poly 37 Jacket 3000

Poly 40 Condenser 3000

P-13 Cooling Twr for P-4Recirculating Poly 1 Jacket 3000

Poly 4 Baffle 3000

Seal H2O Heat Xch 3000

P-13 Cooling Twr for P-5Recirculating Poly 11 Baffle 3000

Poly 12 Jacket 3000

Poly 5 Jacket 3000

P-14 Chilled H2O for P-1Recirculating Poly 21 Jacket 2500

Poly 26 Condenser 2500

Poly 28 Jacket 2500

Poly 33 Condenser 2500

Poly 35 Jacket 2500

P-14 Chilled H2O for P-2Recirculating Poly 1 Jacket 2500

Poly 37 Jacket 2500

Poly 4 Baffle 2500

Poly 40 Condenser 2500

P-14 Chilled H2O for P-5Recirculating Poly 11 Baffle 2500

Poly 12 Jacket 2500

Poly 5 Jacket 2500

P-14 Chillers Recirculating Chiller Unit 1 2500

PolyOne Pedricktown P-1 recirculation U-18 100

Shintech, Inc. Corporate Office Shintech Addis P-1 Recirculating U-28 449

Shintech Freeport P-1 Recirculating U-14A thru F 360

Shintech Plaquemine P-1 Recirculating U-25 433

The Dow Chemical Company Dow Midland - SARAN Resins Vinyl Train R CTW-1 4800

Union Carbide Corporation Union Carbide Texas City P-1, P-2, P-3 Cooling Tower U-14 900

P-2 Cooling Tower U-34 50

P-2, P-3 Cooling Tower U-20 200

Westlake Chemical Corporation Westlake Calvert City P-1 Recirculating U-17 ####

U-22 500

U-30 200

U-40 2000

U-8 100

Westlake Geismar P-1 Recirculating U-13 650

U-3 ####

U-31 1500

Grand Total ####
Reported Emisisons from Cooling Towers - Survey Data Responses

CompanyName FacilityName ProcessUnitIDProcessEquipID ProcessEquipType ExitingProcessEquip TotalVOCOrHAPDesc PoundsBasisForEmissions

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 1,3-Butadiene

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Chlorine

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Ethyl chloride (Chloroethane)

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Ethylene dichloride (1,2-Dichloroethane)

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Ethylene glycol

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Hydrochloric acid

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Methyl chloride (Chloromethane)

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Total VOC

CertainTeed Corporation Lake Charles Polymer Plant P-1 U-13 Cooling Tower EP-4 Vinyl chloride

CertainTeed Corporation Lake Charles Polymer Plant P-2 U-19 Cooling Tower EP-8 1,3-Butadiene

CertainTeed Corporation Lake Charles Polymer Plant P-2 U-19 Cooling Tower EP-8 Ethyl chloride (Chloroethane)

CertainTeed Corporation Lake Charles Polymer Plant P-2 U-19 Cooling Tower EP-8 Ethylene dichloride (1,2-Dichloroethane)

CertainTeed Corporation Lake Charles Polymer Plant P-2 U-19 Cooling Tower EP-8 Ethylene glycol

CertainTeed Corporation Lake Charles Polymer Plant P-2 U-19 Cooling Tower EP-8 Methyl chloride (Chloromethane)

CertainTeed Corporation Lake Charles Polymer Plant P-2 U-19 Cooling Tower EP-8 Total VOC

CertainTeed Corporation Lake Charles Polymer Plant P-2 U-19 Cooling Tower EP-8 Vinyl chloride

OxyVinyls, LP OxyVinyls Pasadena P-11 U-1103 Cooling Tower E-310/E-311/318EP-1117 Other VOC 1410 U-1103 / EP-1117

OxyVinyls, LP OxyVinyls Pasadena P-11 U-1103 Cooling Tower E-310/E-311/318EP-1117 Other VOC 1655 U-1104 / EP-1130

OxyVinyls, LP OxyVinyls Pasadena P-11 U-1103 Cooling Tower E-310/E-311/318EP-1117 Total VOC

OxyVinyls, LP OxyVinyls Pasadena P-11 U-1103 Cooling Tower E-310/E-311/318EP-1117 Vinyl chloride 188 U-1103 / EP-1117

OxyVinyls, LP OxyVinyls Pasadena P-11 U-1103 Cooling Tower E-310/E-311/318EP-1117 Vinyl chloride 361 U-1104 / EP-1130

OxyVinyls, LP OxyVinyls Pedricktown P-6 U-600 Cooling Tower EP-600 Acetaldehyde

OxyVinyls, LP OxyVinyls Pedricktown P-6 U-600 Cooling Tower EP-600 Total VOC

OxyVinyls, LP OxyVinyls Pedricktown P-6 U-600 Cooling Tower EP-600 Vinyl chloride

Shintech, Inc. Corporate OfficeShintech Addis P-1 U-62 COOLING TOWER EP-22 Chlorine 200 Engineering Estimate

Shintech, Inc. Corporate OfficeShintech Addis P-1 U-62 COOLING TOWER EP-22 Ethyl chloride (Chloroethane)

Shintech, Inc. Corporate OfficeShintech Addis P-1 U-62 COOLING TOWER EP-22 Hydrochloric acid

Shintech, Inc. Corporate OfficeShintech Addis P-1 U-62 COOLING TOWER EP-22 Methanol

Shintech, Inc. Corporate OfficeShintech Addis P-1 U-62 COOLING TOWER EP-22 Total VOC 0 Engineering Estimate

Shintech, Inc. Corporate OfficeShintech Addis P-1 U-62 COOLING TOWER EP-22 Vinyl chloride

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Acetaldehyde

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Benzene (including benzene from gasoline)

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Carbon tetrachloride

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Chlorine

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Chloroform

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Ethyl chloride (Chloroethane)

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Ethylene dichloride (1,2-Dichloroethane)

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Ethylidene dichloride (1,1-Dichloroethane)

Shintech, Inc. Corporate Office Shintech, Inc. Corporate OfficeShintech Plaquemine Shintech Plaquemine P-1 U-58 COOLING TOWER COOLING TOWER EP-19 Hydrochloric acid Hydrochloric acid

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Methanol

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Methyl chloride (Chloromethane)

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Total VOC 0 Material Balance

Shintech, Inc. Corporate OfficeShintech Plaquemine P-1 U-58 COOLING TOWER EP-19 Vinyl chloride

The Dow Chemical Company Dow Midland - SARAN ResinsVinyl Train CTW-1 Cooling Tower EP-5 Total VOC 0 Engineering Estimate

The Dow Chemical Company Dow Midland - SARAN ResinsVinyl Train CTW-1 Cooling Tower EP-5 Vinyl chloride 0 Engineering Estimate

The Dow Chemical Company Dow Midland - SARAN ResinsVinyl Train CTW-1 Cooling Tower EP-5 Vinylidene chloride (1,1-Dichloroethylene) 0 Engineering Estimate

Westlake Chemical CorporationWestlake Calvert City P-1 U-89 Cooling Tower EP-26 Hydrochloric acid

Westlake Chemical CorporationWestlake Calvert City P-1 U-89 Cooling Tower EP-26 Methanol

Westlake Chemical CorporationWestlake Calvert City P-1 U-89 Cooling Tower EP-26 Methyl chloride (Chloromethane)

Westlake Chemical CorporationWestlake Calvert City P-1 U-89 Cooling Tower EP-26 Total VOC Material Balance

Westlake Chemical CorporationWestlake Calvert City P-1 U-89 Cooling Tower EP-26 Vinyl chloride Material Balance

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Benzene (including benzene from gasoline)

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Carbon tetrachloride

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Chlorine

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Chlorobenzene

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Chloroform

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Ethyl chloride (Chloroethane)

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Ethylene dichloride (1,2-Dichloroethane)

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Hydrochloric acid

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Tetrachloroethylene (Perchloroethylene)

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Toluene

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Total VOC 0 Engineering Estimate

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Trichloroethylene

Westlake Chemical CorporationWestlake Geismar P-1 U-40 Cooling Water Tower EP-10 Vinyl chloride 0 Engineering Estimate
Section 114 Survey Form C-1-A Data Summary

CompanyName

CertainTeed Corporation

CertainTeed Corporation

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Formosa Plastics Corporation USA

Georgia Gulf Corporation

Georgia Gulf

Oxyvinyls

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP
OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

OxyVinyls, LP

PolyOne Corporation

PolyOne Corporation
Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

Shintech, Inc. Corporate Office

The Dow Chemical Company

The Dow Chemical Company

Westlake Chemical Corporation

Westlake Chemical Corporation

Westlake Chemical Corporation
rvey Form C-1-A Data Summary

FacilityName ProcessUnitIDProcessEquipID

Lake Charles Polymer Plant P-1 U-13

Lake Charles Polymer Plant P-2 U-19

Formosa Plastics Corporation Baton Rouge P-1 U-10

Formosa Plastics Corporation Baton Rouge P-1 U-10

Formosa Plastics Corporation Baton Rouge P-1 U-10

Formosa Plastics Corporation Deleware City P-1 U-14

Formosa Plastics Corporation Deleware City P-1 U-14

Formosa Plastics Corporation Deleware City P-1 U-14

Formosa Plastics Corporation Deleware City P-2 U-73

Formosa Plastics Corporation Deleware City P-2 U-73

Formosa Plastics Corporation Deleware City P-2 U-73

Formosa Plastics Corporation Point Comfort - PVC Unit P-1 U-24

Formosa Plastics Corporation, Point Comfort - Specialty Polyvinyl Chloride (SPVC) Unit P-2 U-17

Georgia Gulf Chemicals Aberdeen Facility 1 U-66, 67, 68, 69

Plaquemine

Deer Park

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1103

OxyVinyls Pasadena P-11 U-1104

OxyVinyls Pasadena P-11 U-1104
OxyVinyls Pasadena P-11 U-1104

OxyVinyls Pasadena P-11 U-1104

OxyVinyls Pasadena P-11 U-1104

OxyVinyls Pasadena P-11 U-1104

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

OxyVinyls Pedricktown P-6 U-600

PolyOne Henry P-13 U-1

PolyOne Henry P-13 U-1
Shintech Addis P-1 U-62

Shintech Freeport P-1 U-45

Shintech Plaquemine P-1 U-58

Dow Midland - SARAN Resins Vinyl Train CTW-1

Dow Midland - SARAN Resins Vinyl Train CTW-1

Westlake Calvert City P-1 U-89

Westlake Calvert City P-1 U-89

Westlake Geismar P-1 U-40
ProcessEquipType ExitingProcessEquipIsSharedSharedProcessUnitID

Cooling Tower EP-4

Cooling Tower EP-8

Cooling Tower No N/A

Cooling Tower No N/A

Cooling Tower EP-16 No N/A

Cooling tower S-2 No

Cooling tower S-3 No

Cooling tower W-8 No

Cooling tower S-2 No

Cooling tower S-3 No

Cooling tower W-8 No

Cooling Tower EP Yes VCM Unit

COOLING TOWER EP-9 No

Cooling Towers EP-12 No

Cooling Tower E-310/E-311/318EP-1117 Yes P10,P12

Cooling Tower E-310/E-311/318S-1118 Yes P10,P12

Cooling Tower E-310/E-311/318S-1119 Yes P10,P12

Cooling Tower E-310/E-311/318S-1120 Yes P10,P12

Cooling Tower E-310/E-311/318S-1121 Yes P10,P12

Cooling Tower E-310/E-311/318S-1122 Yes P10,P12

Cooling Tower E-310/E-311/318S-1123 Yes P10,P12

Cooling Tower E-310/E-311/318S-1124 Yes P10,P12

Cooling Tower E-618/956 EP-1130 Yes P*, P10

Cooling Tower E-618/956 S-1131 Yes P*, P10
Cooling Tower E-618/956 S-1132 Yes P*, P10

Cooling Tower E-618/956 S-1133 Yes P*, P10

Cooling Tower E-618/956 S-1134 Yes P*, P10

Cooling Tower E-618/956 S-1135 Yes P*, P10

Cooling Tower EP-600 Yes P-1

Cooling Tower S-610 Yes P-1

Cooling Tower S-611 Yes P-1

Cooling Tower S-612 Yes P-1

Cooling Tower S-613 Yes P-2

Cooling Tower S-614 Yes P-2

Cooling Tower S-615 Yes P-2

Cooling Tower S-616 Yes P-5

Cooling Tower S-617 Yes P-5

Cooling Tower S-618 Yes P-2

Cooling Tower S-636 No

Cooling Tower S-639 No

Cooling Tower EP-1 No

Cooling Tower S-1 No
COOLING TOWER EP-22 No

COOLING TOWERS EP-13 No

COOLING TOWER EP-19 No

Cooling Tower EP-5 Yes MA Train

Cooling Tower W-9 Yes MA Train

Cooling Tower EP-26 No

Cooling Tower W-8 No

Cooling Water Tower EP-10 No
CertainTeed Corporation Lake Charles Polymer Plant P-1

CertainTeed Corporation Lake Charles Polymer Plant P-1

CertainTeed Corporation Lake Charles Polymer Plant P-1

CertainTeed Corporation Lake Charles Polymer Plant P-2

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Baton Rouge P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Deleware City P1

Formosa Plastics Corporation USAFormosa Plastics Corporation Deleware City P-2

Formosa Plastics Corporation USAFormosa Plastics Corporation Point Comfort - PVC Unit P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Point Comfort - PVC Unit P-1

Formosa Plastics Corporation USAFormosa Plastics Corporation Point Comfort - PVC Unit P-1

Georgia Gulf Corporation Georgia Gulf Chemicals Aberdeen Facility 1

Georgia Gulf Corporation Georgia Gulf Chemicals Aberdeen Facility 1

Georgia Gulf Corporation Georgia Gulf Chemicals Plaquemine Facility P-1

Georgia Gulf Corporation Georgia Gulf Chemicals Plaquemine Facility P-1

Georgia Gulf Corporation Georgia Gulf Chemicals Plaquemine Facility P-1

Georgia Gulf Corporation Georgia Gulf Chemicals Plaquemine Facility P-1

OxyVinyls, LP OxyVinyls Deer Park P-1

OxyVinyls, LP OxyVinyls Deer Park P-1

OxyVinyls, LP OxyVinyls Deer Park P-1

OxyVinyls, LP OxyVinyls Deer Park P-2

OxyVinyls, LP OxyVinyls Deer Park P-2

OxyVinyls, LP OxyVinyls Deer Park P-2

OxyVinyls, LP OxyVinyls Deer Park P-4

OxyVinyls, LP OxyVinyls Deer Park P-4

OxyVinyls, LP OxyVinyls Deer Park P-4

OxyVinyls, LP OxyVinyls Deer Park P-4

OxyVinyls, LP OxyVinyls Deer Park P-4

OxyVinyls, LP OxyVinyls Deer Park P-4

OxyVinyls, LP OxyVinyls Pasadena P1

OxyVinyls, LP OxyVinyls Pasadena P1

OxyVinyls, LP OxyVinyls Pasadena P1

OxyVinyls, LP OxyVinyls Pasadena P1

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10
OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P10

OxyVinyls, LP OxyVinyls Pasadena P11

OxyVinyls, LP OxyVinyls Pasadena P11

OxyVinyls, LP OxyVinyls Pasadena P3

OxyVinyls, LP OxyVinyls Pasadena P3

OxyVinyls, LP OxyVinyls Pasadena P4

OxyVinyls, LP OxyVinyls Pasadena P4

OxyVinyls, LP OxyVinyls Pasadena P5

OxyVinyls, LP OxyVinyls Pasadena P5

OxyVinyls, LP OxyVinyls Pasadena P6

OxyVinyls, LP OxyVinyls Pasadena P6

OxyVinyls, LP OxyVinyls Pasadena P7

OxyVinyls, LP OxyVinyls Pasadena P7

OxyVinyls, LP OxyVinyls Pasadena P8

OxyVinyls, LP OxyVinyls Pasadena P8

OxyVinyls, LP OxyVinyls Pasadena P9

OxyVinyls, LP OxyVinyls Pasadena P9

OxyVinyls, LP OxyVinyls Pedricktown P-1

OxyVinyls, LP OxyVinyls Pedricktown P-2

OxyVinyls, LP OxyVinyls Pedricktown P-3

OxyVinyls, LP OxyVinyls Pedricktown P-3

OxyVinyls, LP OxyVinyls Pedricktown P-3

OxyVinyls, LP OxyVinyls Pedricktown P-3

OxyVinyls, LP OxyVinyls Pedricktown P-5

OxyVinyls, LP OxyVinyls Pedricktown P-6

OxyVinyls, LP OxyVinyls Pedricktown P-6

OxyVinyls, LP OxyVinyls Pedricktown P-6

PolyOne Corporation PolyOne Henry Chilled H2O - L4

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-1

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-2

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-2

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-4

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-4

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-4

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-5

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-5

PolyOne Corporation PolyOne Henry P-13 Cooling Twr for P-5

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-1

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-1
PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-2

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-5

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-5

PolyOne Corporation PolyOne Henry P-14 Chilled H2O for P-5

PolyOne Corporation PolyOne Henry P-14 Chillers

PolyOne Corporation PolyOne Pedricktown P-1

Shintech, Inc. Corporate Office Shintech Addis P-1

Shintech, Inc. Corporate Office Shintech Freeport P-1

Shintech, Inc. Corporate Office Shintech Plaquemine P-1

The Dow Chemical Company Dow Midland - SARAN Resins Vinyl Train

Union Carbide Corporation Union Carbide Texas City P-1, P-2, P-3

Union Carbide Corporation Union Carbide Texas City P-2

Union Carbide Corporation Union Carbide Texas City P-2, P-3

Westlake Chemical Corporation Westlake Calvert City P-1

Westlake Chemical Corporation Westlake Calvert City P-1

Westlake Chemical Corporation Westlake Calvert City P-1

Westlake Chemical Corporation Westlake Calvert City P-1

Westlake Chemical Corporation Westlake Calvert City P-1

Westlake Chemical Corporation Westlake Geismar P-1

Westlake Chemical Corporation Westlake Geismar P-1

Westlake Chemical Corporation Westlake Geismar P-1
Type Unit ID(s) Rate (gpm) Number of HTEX 

Recirculating U-10a 100 3

Recirculating U-10d 100 1

Recirculating U-5a 10000 7

Recirculating U-16a 5000 4

Recirculating PE205A 125 12

Recirculating PE206A 250 12

Recirculating PE206B 250 12

Recirculating PE301 12

Recirculating PE303A/B 12

Recirculating PE304A/B 1500 12

Recirculating PE309 50 12

Recirculating U-14 4000 21

Recirculating U-60 15

Recirculating U-19 46200 4

Recirculating U-3 66300 10

Recirculating U-7 46200 7

Recirculating U-34 thru 45 1000 12

Recirculating U-46 thru 53 1000 9

Recirculating U-166 thru U-173 17000 26

Recirculating U-182 1181 0

Recirculating CTU-175 40000 47

Recirculating CTU-176 22300 10

Recirculating U-102 0 1

Recirculating U-118 0 1

Recirculating U-135 2200 1

Recirculating U-202 0 1

Recirculating U-214 0 1

Recirculating U-231 2200 1

Recirculating U-404 0 2

Recirculating U-410 8400 1

Recirculating U-411 1200 1

Recirculating U-413 8400 1

Recirculating U-414 1600 4

Recirculating U-419 0 4

Recirc U119 44 1

Recirc U120 4 1

Recirc U121 4 1

Recirc U122 4 1

Recirc U1006 200 2

Recirc U1027 1625 1

Recirc U1028 1870 1

Recirc U1030 1625 1

Recirc U1031 1870 2

Recirc U1033 1870 1
Recirc U1034 1870 1

Recirc U1037 1870 1

Recirc U1041 125 1

Recirc U1046 125 1

Recirc U1051 125 1

Recirc U1103 9000 3

Recirc U1104 11600 2

Recirc U300 1265 2

Recirc U308 2100 1

Recirc U400 1265 2

Recirc U408 1350 1

Recirc U500 1265 2

Recirc U508 1350 1

Recirc U600 655 2

Recirc U608 2100 1

Recirc U700 655 2

Recirc U708 1500 1

Recirc U800 655 2

Recirc U808 2100 1

Recirc U900 910 2

Recirc U908 2600 1

recirulating U-100 1200 3

recirulating U-200 1200 3

Recirculating U-303 5 4

Recirculating U-309 30 1

Recirculating U-310 20 3

Recirculating U-311 15 3

recirculation U-508 50 5

Recirculating U-600 13333 4

Recirculating U-611 70 1

recirculation U-616 150 1

Recirculating P-14 Chilled H2O for P-4 2500 15

Recirculating Poly 21 Jacket 3000 33

Recirculating Poly 26 Condenser 3000 33

Recirculating Poly 28 Jacket 3000 33

Recirculating Poly 33 Condenser 3000 33

Recirculating Poly 35 Jacket 3000 33

Recirculating Poly 37 Jacket 3000 10

Recirculating Poly 40 Condenser 3000 10

Recirculating Poly 1 Jacket 3000 15

Recirculating Poly 4 Baffle 3000 15

Recirculating Seal H2O Heat Xch 3000 15

Recirculating Poly 11 Baffle 3000 17

Recirculating Poly 12 Jacket 3000 17

Recirculating Poly 5 Jacket 3000 17

Recirculating Poly 21 Jacket 2500 33

Recirculating Poly 26 Condenser 2500 33

Recirculating Poly 28 Jacket 2500 33

Recirculating Poly 33 Condenser 2500 33

Recirculating Poly 35 Jacket 2500 33
Recirculating Poly 1 Jacket 2500 15

Recirculating Poly 37 Jacket 2500 10

Recirculating Poly 4 Baffle 2500 15

Recirculating Poly 40 Condenser 2500 10

Recirculating Poly 11 Baffle 2500 17

Recirculating Poly 12 Jacket 2500 17

Recirculating Poly 5 Jacket 2500 17

Recirculating Chiller Unit 1 25002

recirculation U-18 1001

Recirculating U-28 4497

Recirculating U-14A thru F 360 20

Recirculating U-25 4336

R CTW-1 48006

Cooling Tower U-14 900 45

Cooling Tower U-34 502

Cooling Tower U-20 200 2800

Recirculating U-17 20000 16

Recirculating U-22 5003

Recirculating U-30 2004

Recirculating U-40 2000 10

Recirculating U-8 1008

Recirculating U-13 6502

Recirculating U-3 12500 15

Recirculating U-31 15003
How Leaks Id'd Freq Method

Not required - not a major source of HAP emissions N/A N/A

Not required - not a major source of HAP emissions N/A N/A

Not required - not a major source of HAP emissions N/A N/A

Not required - not a major source of HAP emissions N/A N/A

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly Method 624

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly Method 624

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly Method 624

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly Method 624

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly Method 624

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly Method 624

The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentratioQuarterly Method 624

Water is sampled weekly. If VOC detected than individual equipment is sampled. Weekly 106

0 0 0

#N/A #N/A #N/A

#N/A #N/A #N/A

#N/A #N/A #N/A

#N/A #N/A #N/A

Sampling of the cooling tower for VCM/EDC/NMHC Twice per day EPA Method 601

Sampling of the chill water tanks for VCM Twice per week EPA Method 601

Sampling of the cooling tower for VCM/EDC/NMHC Twice per day EPA Method 601

#N/A #N/A #N/A

Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. Quarterly EPA Method 107

Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. Quarterly EPA Method 107

High readings identified by the VCM Area Monitoring System requires follow up investigation by Water is not sampled / VCM Area Monitoring Sy Operator with hand held meter0 stem 

Samples caught and analyzed 4 times daily Lab Procedure # PPVC 27, "

Samples caught and analyzed Weekly Lab Procedure # PPVC 27, "

Samples caught and analyzed Weekly Lab Procedure # PPVC 27, "

Process Side flow is not continuous If there were a failure of the exchanger, cooling water would back intothe process side and N/A N/A

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly EPA-107 zers in the area would dete

Weekly testing of the chilled water to detect the presence of VCM. In addition, a GC/MS anlay Weekly / Continuously zer is positioned at the vent of thEPA-107

Process Side flow is not conintuous. If there were a failure of the exchanger, cooling water would back intothe process side anN/A N/A

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly EPA-107 zers in the area would dete

Weekly testing of the chilled water to detect the presence of VCM. In addition, a GC/MS anlay Weekly / Continuously zer is positioned at the vent of thEPA-107

The chilled water is sampled and tested for VCM; Chill Water storage tank has a GC/MS sample point running continuously Weekly EPA-107 wh

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly EPA-107 zers in the area would dete

Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlay Monthly EPA-107 zers in the area would dete

N/A N/A N/A

None N/A 0

0 0 0

N/A N/A N/A

N/A N/A N/A

N/A N/A N/A

N/A N/A N/A

sample only when needed titration

DCS Continuous N/A

DCS Continuous N/A

DCS Continuous N/A

DCS Continuous N/A

Refrigeration machine shutdown N/A N/A
Refrigeration machine shutdown N/A N/A

Refrigeration machine shutdown N/A N/A

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107

The chilled water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly)

N/A N/A N/A

The chilled water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly)

N/A N/A N/A

The chilled water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly)

N/A N/A N/A

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly)

N/A N/A N/A

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly)

N/A N/A N/A

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly)

N/A N/A N/A

The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107 (Weekly)

N/A N/A N/A

GC monitoring of cooling tower airspace every 15 minutes Real-time Gas Chromotogra

GC monitoring of cooling tower airspace every 15 minutes Real-time Gas Chromotogra

0 0 0

HE's are monitored only when unusual conditions are noted. N/A 0

0 0 0

0 0 0

Gas Chromatograph sample point every 15 minutes Real Time Gas Chromatogra

Gas Chromatograph sample point every 15 minutes Real Time Gas Chromatogra

Gas Chromatograph sample point every 15 minutes Real Time Gas Chromatogra

Gas Chromatograph sample point every 15 minutes Real Time Gas Chromatogra

#N/A #N/A #N/A

#N/A #N/A #N/A

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 
Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around e

Method 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Water is sampled for residual VCM per Method 107. If VCM is detected we sy 1/ shift or 2 /day tematically pressure check and sample around eMethod 107 

Pm's by contractor. Check for leaks and amount of Freon 134a lost. Refill and record amount Quarterly 0

Routine sampling of System Once per week Gas Chromotograph

LDAR and NESHAP Quarterly Monitoring Quarterly Method 107

LDAR and NESHAP Quarterly Monitoring daily leak patrol 0

LDAR and NESHAP Quarterly Monitoring Quarterly Method 107

0 Quarterly 415.1

#N/A #N/A #N/A

Vessel testing and leakage into the process when depressurized 5 year pressure test and inspection. N/A

Vessel testing and Cycle Water leakage into process 5 year pressure test and inspection. N/A

Vessel testing and Cycle Water leakage into process 5 year pressure test and inspection. N/A

None 0 0

None 0 0

None 0 0

None 0 0

None 0 0

None 0 0

None 0 0

None 0 0
Location

N/A

N/A

N/A

N/A

Inlet and outlet of cooling tower

Inlet and outlet of cooling tower

Inlet and outlet of cooling tower

Inlet and outlet of cooling tower

Inlet and outlet of cooling tower

Inlet and outlet of cooling tower

Inlet and outlet of cooling tower

Water utility station

0

#N/A

#N/A

#N/A

#N/A

Cooling Tower

Chill water tanks

Cooling Tower

#N/A

Exchanger outlet

Exchanger outlet

0

Cooling Tower Outlet

Cooling Tower Outlet

Cooling Tower Outlet

No

Cooling Tower Basin

Chill water pump discharge

N/A

Cooling Tower Basin

Chill water pump discharge

Chill water pump discharge

Cooling Tower Basin

Cooling Tower pump discharge

N/A

N/A

0

N/A

N/A

N/A

N/A

pump discharge

N/A

N/A

N/A

N/A

N/A
N/A

N/A

Pump discharge.

Pump discharge.

Pump discharge.

Pump discharge

Pump discharge

Pump discharge.

N/A

Pump discharge.

N/A

Pump discharge.

N/A

Pump discharge.

N/A

Pump discharge.

N/A

Pump discharge.

N/A

Pump discharge.

N/A

Stationary sampling point above hot water basin

Stationary sampling point above hot water basin

0

Chilled water storage tank owned and operated by PolyOne.

0

0

air space above hot water basin

air space above hot water basin

air space above hot water basin

air space above hot water basin

#N/A

#N/A

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From Cooling tower as water falls into basin.

From Cooling tower as water falls into basin.

From Cooling tower as water falls into basin.

From Cooling tower as water falls into basin.

From Cooling tower as water falls into basin.

From Cooling tower as water falls into basin.

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps

From sample bleed on outlet of chilled water pumps
From Cooling tower as water falls into basin.

From sample bleed on outlet of chilled water pumps

From Cooling tower as water falls into basin.

From sample bleed on outlet of chilled water pumps

From Cooling tower as water falls into basin.

From Cooling tower as water falls into basin.

From Cooling tower as water falls into basin.

0

Refrigeration Water Collection Tank

Cooling Tower entrance and exit

0

Connectors

CTW inlet and outlet

#N/A

N/A

N/A

N/A

0

0

0

0

0

0

0

0
Heat Exchange Systems - Survey Data Analysis and Summary

OxyVinyls - Pasadena

For El Paso Method...

F Vinyl ChlorideOther VOCTotal VOCTotal VOC C C C in air, ppmv as methane

(gal/min) (lb/yr) (lb/yr) (lb/yr) (lb/hr) (ppmw)(ppbw)

OxyVinyls Pasadena U-1103 9,000 188 1410 1600 0.190 0.042 42.2 3.16

OxyVinyls Pasadena U-1104 11,600 361 1660 2020 0.240 0.041 41.3 3.10

20,600 549 3070 3620 0.430 0.042 41.7 3.13

Formosa - Point Comfort (PVC)

For El Paso Method...

F (gal/min) NMHC, C (ppb) E (lb/hr) C in air, ppmv as methane

46,200 30 0.694 2.25

66,300 30 0.995 2.25

46,200 30 0.694 2.25

158,700 30 2.382 2.25

Formosa - Point Comfort (Specialty PVC)

For El Paso Method...

F (gal/min) NMHC, C (ppb) E (lb/hr) C in air, ppmv as methane

52,900 50 1.32 3.75

Company Facility Unit ID
Heat Exchange Systems - Summary of Clarification Data Submitted to EPA

Company Facility CT # Flow Rate (gpm) Pollutant Measured Leak Action Level Units Monitoring Frequency Monitoring Method Note(s)

1 10,000 Vinyl chloride N/A N/A Weekly Water sampling - GC headspace

2 5,000 Vinyl chloride N/A N/A Weekly Water sampling - GC headspace

Vinyl chloride 10000 ppbw Quarterly Method 415.1

Vinylidene chloride 10000 ppbw Quarterly Method 415.1

Formosa Baton Rouge 1 48,000 Vinyl chloride 10 ppbw Daily Method 601

1 6,000 [no data]

2 3,000 [no data]

Formosa Point Comfort

1 13,500 Vinyl chloride 250 ppbw Quarterly Method 107

2 18,000 Vinyl chloride 250 ppbw Quarterly Method 107

3 18,000 Vinyl chloride 250 ppbw Quarterly Method 107

1 40,000 [cw pressure > process pressure]

2 22,300 [cw pressure > process pressure]

3 1,181 [no heat exchangers]

4 11,000 [utility system]

Vinyl chloride 5000 ppbw Monthly Method 107

Vinyl chloride 1000 ppbw Continuous GC/MS [continuous monitoring of air above cooling tower]

Speciated VOC 5000 ppbw Monthly Method 624

Vinyl chloride 5000 ppbw Monthly Method 107

Vinyl chloride 1000 ppbw Continuous GC/MS [air stripping]

Speciated VOC 5000 ppbw Monthly Method 624

Vinyl chloride 50 ppbw Monthly Method 107

Vinyl chloride 1000 ppbw Continuous GC [continuous monitoring of air above cooling tower]

Speciated VOC 50 ppbw Monthly Method 624

Vinyl chloride 50 ppbw Monthly Method 107

Vinyl chloride 1000 ppbw Continuous GC [continuous monitoring of air above cooling tower]

Speciated VOC 50 ppbw Monthly Method 624

VOC 50 ppbw Monthly El Paso

OxyVinyls Pedricktown 1 13,333 Vinyl chloride 1000 ppbv Continuous Similar to M106 and M21 [continuous monitoring of air above cooling tower]

PolyOne Henry

1 1,900 ammonia and iron N/A N/A Daily N/A

2 1,850 ammonia and iron N/A N/A Daily N/A

Shintech Addis

Shintech Freeport

Shintech Plaquemine

Westlake Calvert City 1 23,000 [no data]

Westlake Geismar 1 10,653 Vinyl chloride 50 ppbw Yearly Method 107

PolyOne Pedricktown

OxyVinyls Pasadena

1 9,000

2 11,600

OxyVinyls Deer Park

1 8,400

2 1,200

Formosa Delaware City

Georgia Gulf Aberdeen

Georgia Gulf Plaquemine

16,500

CertainTeed Lake Charles

Dow Midland 1
ATTACHMENT H: HEAT EXCHANGE SYSTEM MACT FLOOR ANALYSIS

02/08/2012

MACT Floor Analysis - Heat Exchange Systems

Including Formosa - Point Comfort Survey Data

Systems That Monitor for VOC Using Modified El Paso or Water Sampling Method

Company Facility CT # Flow Rate (gpm) Pollutant MeasuredLeak Action LevelUnitsMonitoring FrequencyMonitoring MethodNote(s)

Formosa Point Comfort 1 46,200 NMHC 30 ppbwWeekly Method 601

Formosa Point Comfort 2 66,300 NMHC 30 ppbwWeekly Method 601

Formosa Point Comfort 3 46,200 NMHC 30 ppbwWeekly Method 601

OxyVinyls Pasadena 1 9,000 Speciated VOC 50 ppbw Monthly Method 624 1

OxyVinyls Pasadena 2 11,600 Speciated VOC 50 ppbw Monthly Method 624 2

OxyVinyls Pasadena 2 11,600 VOC 50 ppbw Monthly El Paso 3

Formosa Point Comfort (SPVC) 1 52900 NMHC 50 ppbw Twice-Daily Method 601

OxyVinyls Deer Park 1 8,400 Speciated VOC 5000 ppbw Monthly Method 624 4

OxyVinyls Deer Park 2 1,200 Speciated VOC 5000 ppbw Monthly Method 624 5

Cooling Water Conc. Existing 50 ppbw [LAL floor determined from median LAL of top 5 systems that monitor for VOC using El Paso or water sampling method]

New 50 ppbw

Stripping Gas Conc. Existing 3.9 ppmv

New 3.9 ppmv

Delay of Repair Cooling Water Conc. 500 ppbw

Stripping Gas Conc. 39 ppmw

Systems That Monitor for Vinyl Chloride Using Method 107

Company Facility CT # Flow Rate (gpm) Pollutant MeasuredLeak Action LevelUnitsMonitoring FrequencyMonitoring MethodNote(s)

OxyVinyls Pasadena 1 9,000 Vinyl chloride 50 ppbw Monthly Method 107 1

OxyVinyls Pasadena 2 11,600 Vinyl chloride 50 ppbw Monthly Method 107 2

Westlake Geismar 1 10,653 Vinyl chloride 50 ppbw Yearly Method 107 3

Georgia Gulf Aberdeen 1 13,500 Vinyl chloride 250 ppbwQuarterly Method 107 4

Georgia Gulf Aberdeen 2 18,000 Vinyl chloride 250 ppbwQuarterly Method 107 5

Georgia Gulf Aberdeen 3 18,000 Vinyl chloride 250 ppbwQuarterly Method 107

OxyVinyls Deer Park 1 8,400 Vinyl chloride 5000 ppbw Monthly Method 107

OxyVinyls Deer Park 2 1,200 Vinyl chloride 5000 ppbw Monthly Method 107

Cooling Water Conc. Existing 50 ppbw [LAL floor determined from median LAL of top 5 systems that monitor for vinyl chloride using Method 107]

New 50 ppbw

Delay of Repair Cooling Water Conc. 500 ppbw
ATTACHMENT D/H: HEAT EXCHANGE SYSTEM COST ANALYSIS

02/08/2012

Heat Exchange Systems - Summary of Clarification Data Submitted to EPA Calculated Emissions, Reductions, and Costs

OVP Conc (ppbw) 5.93

% of LAL 12%

Avg LAL (ppbw) 1363 Based on M107 only

Avg Conc (ppbw) 162

LAL (ppbw) 50 Cost per Repair ($/tower/yr) 4300

DOR LAL (ppbw) 800

DOR Period (days) 120

Repairs per yr 1

REPORTED 

EMISSIONS 

FROM 

VC Conc LAL BASELINE 

EMISSIONS

EMISSION 

REDUCTIONS REPAIR COSTS

Company Facility CT # Flow Rate (gpm) Pollutant Measured Leak Action Level Units Monitoring Frequency Monitoring Method Note(s) VC (tpy) (ppbw) (ppbw) VC (tpy) VC (tpy) ($/yr)

1 10,000 Vinyl chloride Weekly Water sampling - GC headspace 162 1363 3.54E+00 2.45E+00 4,300

2 5,000 Vinyl chloride Weekly Water sampling - GC headspace 162 1363 1.77E+00 1.22E+00 4,300

Vinyl chloride 10000 ppbw Quarterly Method 415.1 1186 10000 4.29E+01 4.11E+01 4,300

Formosa Baton Rouge 1 48,000 Vinyl chloride 10 ppbw Daily Method 601 1 10 1.25E-01 0.00E+00 4,300

1 6,000 [no data] 162 1363 2.13E+00 1.47E+00 4,300

2 3,000 [no data] 162 1363 1.06E+00 7.34E-01 4,300

Formosa Point Comfort 158700 162 1363 5.62E+01 3.88E+01 4,300

1 13,500 Vinyl chloride 250 ppbw Quarterly Method 107 30 250 8.78E-01 0.00E+00 4,300

2 18,000 Vinyl chloride 250 ppbw Quarterly Method 107 30 250 1.17E+00 0.00E+00 4,300

3 18,000 Vinyl chloride 250 ppbw Quarterly Method 107 30 250 1.17E+00 0.00E+00 4,300

1 40,000 [cw pressure > process pressure] 4,300

2 22,300 [cw pressure > process pressure] 4,300

3 1,181 [no heat exchangers] 4,300

4 11,000 [utility system] 4,300

Vinyl chloride 5000 ppbw Monthly Method 107 593 5000 1.09E+01 1.00E+01 4,300

Vinyl chloride 5000 ppbw Monthly Method 107 593 5000 1.56E+00 1.43E+00 4,300

Vinyl chloride 50 ppbw Monthly Method 107 9.40E-02 6 50 9.40E-02 0.00E+00 4,300

Vinyl chloride 50 ppbw Monthly Method 107 1.81E-01 6 50 1.81E-01 0.00E+00 4,300

OxyVinyls Pedricktown 1 13,333 Vinyl chloride 1000 ppbv Continuous Similar to M106 and M21 [continuous monitoring of air above cooling tower] 119 1000 3.47E+00 2.01E+00 4,300

PolyOne Henry 39000 162 1363 1.38E+01 9.54E+00 4,300

1 1,900 162 1363 6.73E-01 4.65E-01 4,300

2 1,850 162 1363 6.55E-01 4.53E-01 4,300

Shintech Addis 449 162 1363 1.59E-01 1.10E-01 4,300

Shintech Freeport 360 162 1363 1.28E-01 8.81E-02 4,300

Shintech Plaquemine 433 162 1363 1.53E-01 1.06E-01 4,300

Westlake Calvert City 1 23,000 [no data] 162 1363 8.15E+00 5.63E+00 4,300

Westlake Geismar 1 10,653 Vinyl chloride 50 ppbw Yearly Method 107 6 50 1.39E-01 0.00E+00 4,300

151.1 115.6 116,100

CertainTeed Lake Charles

Dow Midland 1 16,500

Formosa Delaware City

Georgia Gulf Aberdeen

Georgia Gulf Plaquemine

OxyVinyls Deer Park

1 8,400

2 1,200

9,000

2 11,600

PolyOne Pedricktown

OxyVinyls Pasadena

1
ATTACHMENT D/H: HEAT EXCHANGE SYSTEM COST ANALYSIS

02/08/2012

Calculated Emissions, Reductions, and Costs

Total Capital Cost Ttal Annual Cost

Control EquipT&M $ $/yr VCM HCl D/F TOH VCM HCl D/F TOH

Control Testing and Control Control Testing and Testing and Total Total Baseline - Baseline - Baseline - Baseline - Reduction - Reduction - Reduction - Reduction - 

Certain Teed - Lake Charles Area Source Bulk 8,600 5.31E+00 5.31E+00 3.67E+00 3.67E+00

PolyOne - Henry PVC - Only Suspension, Dispersion, Suspension Blending 4,300 1.38E+01 1.38E+01 9.54E+00 9.54E+00

PolyOne - Pedricktown PVC - Only Dispersion 8,600 1.33E+00 1.33E+00 9.18E-01 9.18E-01

Formosa - Delaware City PVC - Only Dispersion, Copolymer (VACO-D) 8,600 3.19E+00 3.19E+00 2.20E+00 2.20E+00

Dow - Midland PVC - Combined Copolymer (VDCO-S) 4,300 4.29E+01 4.29E+01 4.11E+01 4.11E+01

Formosa - Baton Rouge PVC - Combined Suspension 4,300 1.25E-01 1.25E-01 0.00E+00 0.00E+00

Formosa - Point Comfort PVC - Combined Suspension 4,300 5.62E+01 5.62E+01 3.88E+01 3.88E+01

Georgia Gulf - Aberdeen PVC - Only Suspension 12,900 3.22E+00 3.22E+00 0.00E+00 0.00E+00

Georgia Gulf - Plaquemine PVC - Combined Suspension 17,200 0.00E+00 0.00E+00 0.00E+00 0.00E+00

OxyVinyls - Deer Park PVC - Combined Suspension 8,600 1.25E+01 1.25E+01 1.14E+01 1.14E+01

OxyVinyls - Pasadena PVC - Only Suspension 8,600 2.75E-01 2.75E-01 0.00E+00 0.00E+00

OxyVinyls - Pedricktown PVC - Only Suspension 4,300 3.47E+00 3.47E+00 2.01E+00 2.01E+00

Shintech - Addis PVC - Only Suspension 4,300 1.59E-01 1.59E-01 1.10E-01 1.10E-01

Shintech - Freeport PVC - Only Suspension 4,300 1.28E-01 1.28E-01 8.81E-02 8.81E-02

Shintech - Plaquemine PVC - Combined Suspension 4,300 1.53E-01 1.53E-01 1.06E-01 1.06E-01

Westlake - Calvert City PVC - Combined Suspension 4,300 8.15E+00 8.15E+00 5.63E+00 5.63E+00

Westlake - Geismar PVC - Combined Suspension 4,300 1.39E-01 1.39E-01 0.00E+00 0.00E+00

MACT Floor Costs Baseline Emissions and MACT Floor Emissions Reductions

MACT Floor Capital Cost ($) MACT Floor - Annual Costs ($/yr) Baseline Emissions (TPY) MACT Floor Emissions Reductions (TPY)

Control Equip T&M
COOLING TOWERS - Count for PVC HeatExch

CompanyNam

e

FacilityName Proces

s

Num of 

CTs CT ID Total Flow, gpm

# of HeatEx 

In System lb water/yr How Leaks Id'd Freq Method

Location How Leaks 

Id'd Freq Method

Location

CertainTeed Lake Charles B 1 U-13 10200 11 4.29E+10 Not required - not a major source of HAP emissions N/A N/A N/A

CertainTeed Lake Charles B 1 U-19 5000 4 2.10E+10 Not required - not a major source of HAP emissions N/A N/A N/A

Formosa Baton Rouge S 1 U-10 2175 84 9.14E+09 The cooling tower water inlet and outlet was sampled quarterly in 2008 and tested using Method 624 to determine concentration of specific HAPs in the cooling water. QuarterlyMethod 624 Inlet and outlet of cooling tower

Formosa Delaware City D 1 U-14 4000 21 1.68E+10 Water is sampled weekly. If VOC detected than individual equipment is sampled. Weekly 106 Water utility station

Formosa Delaware City D 1 U-73 4000 21 1.68E+10

Formosa Point Comfort - PVC S 1 U-24 158700 21 6.67E+11 Sampling of the cooling tower for VCM/EDC/NMHC Twice per day EPA Method 601 Cooling Tower Sampling of the chill water tanks for VCM Twice per week EPA Method 601 Chill water tanks

Formosa Point Comfort - Specialty Polyvinyl Chloride (SPVC) Unit S, O 1 U-17

Georgia Gulf Aberdeen S 1 U-66 2000 21 8.41E+09 Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. QuarterlyEPA Method 107 Exchanger outlet

Georgia Gulf Aberdeen S 1 U-67 2000 21 8.41E+09 Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. QuarterlyEPA Method 107 Exchanger outlet

Georgia Gulf Aberdeen S 1 U-68 2000 21 8.41E+09 Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. QuarterlyEPA Method 107 Exchanger outlet

Georgia Gulf Aberdeen S 1 U-69 2000 21 8.41E+09 Cooling water is obtained from the exhanger outlets and anaylyzed for VCM concentration. QuarterlyEPA Method 107 Exchanger outlet

Georgia Gulf Plaquemine S 1 unknown - assume 2 CTs 40000 47 1.68E+11 Samples caught and analyzed Weekly Lab Procedure # PPVC 27, "Residual Vinyl Chloride using Perkin Elmer HS40B" Cooling Tower Outlet

Georgia Gulf Plaquemine S 1 unknown - assume 2 CTs 22300 10 9.37E+10 Samples caught and analyzed Weekly Lab Procedure # PPVC 27, "Residual Vinyl Chloride using Perkin Elmer HS40B" Cooling Tower Outlet

OxyVinyls Deer Park S 1 unknown - assume 3 CTs 2200 3 9.25E+09 Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlayzers in the area would detect fugitive VCM.

OxyVinyls Deer Park S 1 unknown - assume 3 CTs 2200 3 9.25E+09 Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlayzers in the area would detect fugitive VCM.

OxyVinyls Deer Park S 1 unknown - assume 3 CTs 19600 13 8.24E+10 Monthly testing of the cooling tower water to detect the presence of VCM. In addition, GC/MS anlayzers in the area would detect fugitive VCM.

OxyVinyls Pasadena S 1 U-1103 9000 3 3.78E+10 The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107Pump discharge

OxyVinyls Pasadena S 1 U-1104 11600 2 4.88E+10 The cooling water is sampled. The sample is analyzed for VCM. Weekly & Monthly EPA107Pump discharge

OxyVinyls Pedricktown S 1 U-600 13333 4 5.60E+10 Gas Chromatograph sample point every 15 minutes Real Time Gas Chromatography air space above hot water basin

PolyOne Henry S, D 1 U-1 39000 281 1.64E+11 Water is sampled for residual VCM per Method 107. If VCM is detected we sytematically pressure check and sample around each process unti for RVCM. W 1/ shift or 2 /day Method 107 From sample bleed on outlet of chilled water pumps Water is sampled for residual VCM per Method 107. If VCM is detected we sytematically pressure 1/ shift or 2 /day Method 107 From Cooling tower as water falls into basin. e systematically stagger eq

PolyOne Pedricktwon D 1 U-18 100 1 4.20E+08 Routine sampling of System Once per week Gas Chromotograph Refrigeration Water Collection Tank

Shintech Addis S 1 U-62 449 7 1.89E+09 LDAR and NESHAP Quarterly Monitoring QuarterlyMethod 107 Cooling Tower entrance and exit

Shintech Shintech Freeport Freeport S 1 U-45 360 20 1.51E+09 1.51E+09 LDAR and NESHAP Quarterly Monitoring LDAR and NESHAP Quarterly Monitoring daily leak patrol daily leak patrol 0 0

Shintech Plaquemine S 1 U-58 433 6 1.82E+09 LDAR and NESHAP Quarterly Monitoring QuarterlyMethod 107 Connectors

Dow Midland S 1 CTW-1 4800 6 2.02E+10 Quarterly 415.1 CTW inlet and outlet

Westlake Calvert City S 1 U-89 22800 41 9.58E+10 None

Westlake Geismar S 1 U-40 14650 20 6.16E+10 None