Test ID: 4-24-13 Courtyard B Reactor 4-2 **Value** 0.0001 0 0.0001

250.00 175.00 0.0012 0.0000 0.0000 200.00 200.00 0.0012

200.00 250.00 0.0034 0.0034

1200.00 1000.00 0.0001 0 0.00010

**Value** 3.5000 1.3000 4.8000 1A Filter W eight (g)

Total mg of Particulate MCEM **Total mg of MCEM MCEM Analysis Calculations**  1B QC Filter Blank (g) Net MCEM From Filter (g)

Volume of Acetone Used 2A (ml) Volume of MC Used 2M (ml) 2M W eight of MCEM From Front Half Glassware Rinses (g)

Volume of Acetone Used 3A (ml) Volume of MC Used 3M (ml) 3M W eight of MCEM From Back Glassware Rinses (g) 3M Net of MCEM Adjusted from Blanks (g)



## A398 Reactor

3W B W eight of MCEM From Blank (g) 3WNet of Extracted W ater Adjusted from Blank (g)

Total mg of Gaseous MCEM Volume of Deionized W ater Used 3W(ml) Volume of Deionized W ater Used in Blank (ml) 2M Net MCEM Adjusted from Blank (g) 4A W eight of Acetone Blank (g) 4M W eight of MC Blank (g) Volume of MC Used in Blank (ml) Volume of Acetone Used in Blank (ml)

3WW eight of Impinger W ater Plus Back Half Rinses Extracted (g)



## 4/24/2013

**MCEM Analysis Data**Test ID: 4-24-13 Courtyard B Reactor 4-2



### Value 0.4998 0.84 20.9 0
28.836 28.68808152 0.013650653 559.9 702.2 29.75 54 1.88 1.008 29.75 120 1.56 90.099 25.1 29.74 0.3 0.00049087385



### Value 85.4871051 32.56117 4.5 0.21182 20.6 0.97129 0.013651 0.045719 100.7652 I = % Isokinetic variation 

### Air Test Calculations

 Hav g= average orifice meter differential Vm = Total sample volume from dry gas meter (dcf) Vlc Volume collected Ps = Absolute stack gas pressure (in Hg)

Vwc (std) = conv erted water v olume Total silica gel catch (ml) Vwsg (std) = conv erted silica gel water v olume Bws = fraction of gas that is moisture Vwc(std) Nozzle diameter (in) Area of Nozzle (ft^2)

Vm (std) = Volume of sample measured by DGM (dscf) Vs = Average stack gas v elocity Total impinger catch (ml)  H@ = Orifice meter calibration factor, (in. water) Y = Dry gas meter calibration factor Pbar = Barometric pressure, (in. Hg) Total sampling time required for test (min) Tm = Absolute average dry gas meter temp (R). Ts = Stack gas absolute av erage temperature (R) Pm = Pressure at orifice meter (in. Hg) Ta = Sampling site ambient temperature, (°F) Md = Stack gas dry molecular weight, (lb/lb-mole) Ms = Stack gas (wet) molecular weight (lb/lb-mole) Bws = Stack gas moisture content % O 2 in Gas Stream %CO 2 in Gas Stream 

## A3 **98 Reactor**

**4/24/2013**

**Method 5 Parameter**
 p = Stack gas v elocity pressure (av g. sqrt  p - in. water) Cp = Pitot tube calibration coefficient

### Test ID: 4-24-13 Courtyard B Reactor 4-2

**Value** 3.5000 0.0035 1.3 0.0013 85.48710515 32.5612 702.2 29.75 29.74 12.57 0.013650653 1086228.127 0.10 2.35 0.04 0.87 0.0409 0.0152 **0.0561**

**ACFM 24557.64**  **SCFM 18354.35**  **DSCFM 18103.80212** 

Total g of MCEM in Particulate Sample Total mg of MCEM in Gaseous Sample



## A398 Reactor **4/24/2013**

**Combined Method 5 Parameter and Analytical**

Total g of MCEM in Gaseous Sample Total mg of MCEM in Particulate Sample

Vm(std) Volume of Air Sampled by DGM (dscf) Vs Velocity of Wet Scrubber During Test (ft/s) Tr Average Temperature Wet Scrubber During Test (°R) Pbar Barometric Pressure During Test (in Hg)

Area of Stack (ft2) Ps = Absolute stack gas pressure (in Hg)

Bws Moisture in Wet Scrubber Emissions Qstd Flow of Roof Vent Emissions (dscf/hr) Emission Rate of Gaseous MCEM lb/hr Emission Rate of Gaseous MCEM lb/d

**Concentration of Total MCEM mg/dscf** Emission Rate of Particulate MCEM lb/hr Emission Rate of Particulate MCEM lb/d Concentration of Gaseous MCEM mg/dscf Concentration of Particulate MCEM mg/dscf

## Value 5.7 0.00570 85.487105 32.561172 702.2 29.75 12.57 0.0136507 1086228.1

**Value** 0.160 3.829 0.0667 Emission Rate of Particulate lb Particulate/hr Emission Rate of particulate lb particulate/d Concentration of Particulate mg/dscf Area of the Dry Scrubber Bws Moisture in Roof Emissions Qstd Flow of Roof Vent Emissions (dscf/hr) 

## Combined Method 5 Parameter and Analy **tical** 

## North Wet Scrubber Emission Calculations

**4/24/2013**

**Air Test Final Results** Total mg of Particulate Total g of Particulate Vm(std) Volume of Air Sampled by DGM (dscf) Vs Average stack gas velocity Ts Stack Gas R o 

### Pbar Barometric Pressure During Test (in Hg)