EMISSIONS TEST REPORT 

BIG BEND STATION 

FACILITY ID NUMBER: 0570039 

EMISSION UNIT ID NO: -002 

UNIT 2 

PARTICULATE MATTER, SULFUR DIOXIDE, and 

VISIBLE EMISSIONS 

October 26, 2006 

Prepared For: 

Tampa Electric Company 

Big Bend Station 

P.O. Box 111 

Tampa, Florida 33601-0111 

Prepared By: 

Tampa Electric Company 

Environmental, Health & Safety 

Environmental Services 

Air Services Group 

Environmental Services 

Air Services Group 

5010 Causeway Boulevard 

Tampa, Florida 33619- 6130 
REPORT CERTIFICATION 

 The sampling and subsequent data entry/reduction detailed in this report 

was conducted at my direction, and I hereby certify that this test report is 

authentic and accurate to the best of my knowledge. 

Signature:__________________________ 

Jorge A. Varino 

Environmental Technician 

Test Team Lead 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the test performance, associated quality assurance 

activities, the resultant calculations, and the contents of this report, and certify 

that all project quality objectives have been met. This report is approved for 

submittal. 

Signature:__________________________ 

Raymond A. McDarby, Jr. 

Senior Environmental Technician 

Quality Assurance/Quality Control Specialist 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the testing details and results submitted in this report, 

and hereby certify that this test report is authentic and accurate to the best of 

my knowledge. 

Signature:__________________________ 

David A. Smith 

Coordinator – Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 
TABLE OF CONTENTS

SECTION PAGE NO.

1.0 SUMMARY OF RESULTS 1 

2.0 DISCUSSION OF RESULTS 2 

3.0 SOURCE DESCRIPTION / TEST PROCEDURES 3 

4.0 TABULATED RESULTS 

SOOT BLOWING PARTICULATE TEST SUMMARY 6 

NON SOOT BLOWING PARTICULATE TEST SUMMARY 7 

SULFUR DIOXIDE INFORMATION SUMMARY 8 

SOOT BLOWING OPACITY DATA SUMMARY 9 

NON SOOT BLOWING OPACITY DATA SUMMARY 10 

HEAT INPUT CALCULATIONS 11 

 4.0 FIGURES 

FIGURE 1 SAMPLING LOCATION DIAGRAM 13 

APPENDICES

A. PARTICULATE MATTER CALCULATIONS

B. PARTICULATE MATTER LABORATORY ANALYTICAL DATA

C. BOILER/PRECIPITATOR OPERATIONAL DATA

D. PLANT CEMS DAHS PRINTOUTS

E. FUEL ANALYSIS

F. FIELD DATA SHEETS

G. SAMPLING EQUIPMENT CALIBRATIONS

H. CHAIN OF CUSTODY

I. TEST PARTICIPANTS
1.0 INTRODUCTION

On October 26, 2006, Tampa Electric Company’s, Environmental Services, Air 

Services Group, performed source emission tests at the Big Bend Station, Boiler 

No. 2, emissions unit I.D.# 0570039-002. Testing was conducted according to 

procedures stipulated by the Florida Department of Environmental Protection 

(FDEP) for fossil fuel steam generators. Testing was conducted in accordance 

with the Title V Permit #0570039-021-AV, Conditions A.12. 

1 
2.0 DISCUSSION OF RESULTS

The particulate matter emission rate under both soot blowing, and non-soot 

blowing conditions were derived from three United States Environmental 

Protection Agency (USEPA) Reference Method 5B test runs. Under soot blowing 

conditions the average of the three test runs was 0.03 lb/mmBtu. Under nonsoot blowing conditions the average of the three test runs was 0.02 lb/mmBtu. 

The USEPA Consent Decree allowable emission rate under either condition is 

0.03 lb/mmBtu. 

The Sulfur Dioxide (SO2) emission rate was determined using data provided by 

the Continuous Emissions Monitoring System’s (CEMS), Data Acquisition and 

Handling System (DAHS). The average emission rate for the test period was 

determined to be 0.2 lb/mmBtu, and 657 lbs/hr. The FDEP allowable emission 

rate is 6.5 lbs/mmBtu based on a two hour average, and 3277 lbs/hr based on 

scenario 3 as listed in condition A.9 of the permit. 

Visible emissions were evaluated using a United Sciences, Incorporated, Model 

500C transmissometer (S/N 5001689), during both soot blowing and non-soot 

blowing testing. The 1-hour average opacity under soot blowing conditions was 

7%. The 1-hour average opacity under non-soot blowing conditions was 9%. 

The FDEP allowable emission rate is 20 percent opacity. 

During the test performed on October 26, 2006, Boiler No. 2 was operated at an 

average heat input rate of 3584 mmBtu/hr. The average quantity of fuel burned 

was 152.0 tons per hour. Based on the permitted maximum heat input rate of 

3996 mmBtu/hr, the capacity factor for this test was determined to be 90%. 

2 
3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Big Bend Station is located on Big Bend Road, Ruskin, Florida at UTM 

coordinates East 361.9 North 3075.0. The Boiler No. 2 particulate matter 

sampling location consists of a shared circular stack 29.83 feet in diameter with 

four sample ports located 90 degrees apart on the stack circumference. These 

ports are located downstream of the electrostatic precipitator and the FGD 

scrubber. The sampling ports were determined to be 8.74 diameters 

downstream of the transition ductwork and 2.42 diameters upstream of the stack 

exit. Using these criteria, a total of 12 sampling points were chosen for 

particulate sampling as stipulated in the USEPA Method 1 test procedure. During 

this test, Boiler No. 1 was not operating, and was isolated from the FGD module. 

A diagram of the stack sampling location is included in Figure 1 along with other 

pertinent information on the test site. 

Boiler No. 2 is serviced by an electrostatic precipitator for the control of flyash 

emissions, and a flue gas desulfurization (FGD) system for control of sulfur 

dioxide emissions. Generator and precipitator operations data is included in 

Appendix C of this report. 

Particulate sampling was performed according to USEPA Method 5B 

"Determination of Nonsulfuric Acid Particulate Matter from Stationary Sources". 

Individual test run calculations are included as Appendix A of this report. 

Particulate matter laboratory analysis may be found in Appendix B of this report. 

Diluent gas sampling and analysis was performed according to USEPA Method 

3B "Gas Analysis for Determination of Emission Rate Correction Factor, or 

Excess Air”. Gas analysis was performed on-site using an Orsat analyzer. 

Sulfur Dioxide (SO2) and Carbon Dioxide (CO2) data were provided by the 

Continuous Emissions Monitoring System (CEMS), Data Acquisition and 

3 
Handling System (DAHS). Averages were derived from the time frame of 8:15 

through 17:15 on October 26, 2006. This data is included as Appendix D of this 

report. 

Visible emissions were assessed using the installed Continuous Opacity Monitor 

(COM), and the CEMS DAHS. 

4 
4.0 TABULATED RESULTS

5 
BIG BEND STATION

PARTICULATE MATTER DATA SUMMARY

Run 2s Run 3s Run 4s

Vm(std), scf 36.982 36.312 36.167

Bws, ratio 0.12101 0.15952 0.16125

O2, % volume 9 11 10.5

Md, lb/lb - mole 29.96 29.96 30.02

Ms, lb/lb - mole 28.51 28.05 28.08

Qs, acf/min 1259894.6 1241871.7 1237879.0

Qs(std), dscf/min 997948.2 939910.9 936644.1

I, % 100.1 104.3 104.3

C, lbs/dscf 1.01E-06 1.86E-06 1.44E-06

Er, lb/mmBtu 0.017 0.038 0.028

Emission rate (Er), lb/mmBtu, calculated as: C x 9780 dscf/mmBtu x (20.9/(20.9-%O2))

102.90

1.4386E-06

0.0281

29.980

28.216

1246548.42

958167.74

Test Summary

36.487

0.147259

10.17

Boiler #2

WET-BOTTOM UTILITY BOILER

October 26, 2006

SOOT BLOWING

6 
BIG BEND STATION

PARTICULATE MATTER DATA SUMMARY

Run 1 Run 2 Run 3

Vm(std), scf 38.094 36.586 36.747

Bws, ratio 0.10618 0.15558 0.15501

O2, % volume 9 10.5 10.5

Md, lb/lb - mole 29.96 29.94 29.94

Ms, lb/lb - mole 28.69 28.08 28.09

Qs, acf/min 1298171.6 1255417.7 1253792.6

Qs(std), dscf/min 1046781.9 955294.1 956950.7

I, % 98.3 103.4 103.7

C, lbs/dscf 1.05E-06 8.53E-07 9.09E-07

Er, lb/mmBtu 0.018 0.017 0.018

Emission rate (Er), lb/mmBtu, calculated as: C x 9780 dscf/mmBtu x (20.9/(20.9-%O2))

9.3730E-07

0.0176

NON - SOOT BLOWING

28.287

1269127.30

986342.25

101.80

37.143

0.138925

10.00

29.947

Boiler #2

WET-BOTTOM UTILITY BOILER

October 26, 2006

Test Summary

7 
BIG BEND STATION

SULFUR DIOXIDE DATA FROM CEMs

Test Period Information

Start Time 8:15:00 Eastern Standard Time (EST)

Stop Time 17:15:00 Eastern Standard Time (EST)

Total Time 9:00:00

Corresponding to the time frame for the PM test.

Sulfur Dioxide Data:

SO2 CO2 SO2 SO2

ppmvw %, wet lb/mmBtu lbs/hr

55.87 10.02 0.2 657

Calculation Details

SO2, lb/mmBtu = SO2, ppmvw x Cf x Fc x (100 / CO2 %, wet)

where:

Cf = 1.6635E-07 (lb/scf)/ppm SO2

Fc = 1800 scf/mmBtu

SO2, lbs/hr = SO2, lb/mmBtu x Heat Input, mmBtu/hr

where:

Heat Input = 3936 mmBtu/hr, from Heat Input Calculation

Unit #2

WET-BOTTOM UTILITY BOILER

October 26, 2006

CEM DATA RM - 19

8 
Facility: Big Bend Station

Unit: Unit 2

Operating Conditions: Sootblowing

Record# DATE TIME OPACITY2 Record# DATE TIME OPACITY2

1 10/26/06 9:44 7.9 31 10/26/06 10:14 6.8

2 10/26/06 9:45 7.5 32 10/26/06 10:15 6.8

3 10/26/06 9:46 7.3 33 10/26/06 10:16 7.4

4 10/26/06 9:47 7.4 34 10/26/06 10:17 6.9

5 10/26/06 9:48 7.3 35 10/26/06 10:18 6.5

6 10/26/06 9:49 7.5 36 10/26/06 10:19 6.6

7 10/26/06 9:50 7.0 37 10/26/06 10:20 6.7

8 10/26/06 9:51 6.9 38 10/26/06 10:21 6.8

9 10/26/06 9:52 6.9 39 10/26/06 10:22 6.8

10 10/26/06 9:53 6.6 40 10/26/06 10:23 7.3

11 10/26/06 9:54 6.8 41 10/26/06 10:24 7.5

12 10/26/06 9:55 7.7 42 10/26/06 10:25 7.0

13 10/26/06 9:56 7.6 43 10/26/06 10:26 6.8

14 10/26/06 9:57 7.1 44 10/26/06 10:27 6.8

15 10/26/06 9:58 7.2 45 10/26/06 10:28 6.9

16 10/26/06 9:59 7.1 46 10/26/06 10:29 7.0

17 10/26/06 10:00 6.6 47 10/26/06 10:30 7.1

18 10/26/06 10:01 7.2 48 10/26/06 10:31 7.5

19 10/26/06 10:02 7.5 49 10/26/06 10:32 7.2

20 10/26/06 10:03 7.1 50 10/26/06 10:33 7.2

21 10/26/06 10:04 6.9 51 10/26/06 10:34 7.1

22 10/26/06 10:05 6.7 52 10/26/06 10:35 7.1

23 10/26/06 10:06 6.6 53 10/26/06 10:36 7.2

24 10/26/06 10:07 7.2 54 10/26/06 10:37 7.3

25 10/26/06 10:08 7.3 55 10/26/06 10:38 7.1

26 10/26/06 10:09 7.3 56 10/26/06 10:39 7.1

27 10/26/06 10:10 7.1 57 10/26/06 10:40 7.8

28 10/26/06 10:11 7.1 58 10/26/06 10:41 7.4

29 10/26/06 10:12 6.5 59 10/26/06 10:42 8.1

30 10/26/06 10:13 6.7 60 10/26/06 10:43 8.5

Test Average: 7.14 %

Minimum One Minute Average: 6.50 %

Maximum One Minute Average: 8.50 %

Maximum Six Minute Average: 7.78 %

Visible Emissions Determination from Opacity Monitor

9 
Facility: Big Bend Station

Unit: Unit 2

Operating Conditions: Non-sootblowing

Record# DATE TIME OPACITY2 Record# DATE TIME OPACITY2

1 10/26/06 8:15 8.5 31 10/26/06 8:45 8.9

2 10/26/06 8:16 8.3 32 10/26/06 8:46 8.8

3 10/26/06 8:17 8.4 33 10/26/06 8:47 8.5

4 10/26/06 8:18 8.4 34 10/26/06 8:48 8.8

5 10/26/06 8:19 8.7 35 10/26/06 8:49 8.7

6 10/26/06 8:20 8.9 36 10/26/06 8:50 8.6

7 10/26/06 8:21 8.8 37 10/26/06 8:51 8.3

8 10/26/06 8:22 9.0 38 10/26/06 8:52 8.2

9 10/26/06 8:23 8.3 39 10/26/06 8:53 8.3

10 10/26/06 8:24 8.3 40 10/26/06 8:54 8.4

11 10/26/06 8:25 8.4 41 10/26/06 8:55 8.2

12 10/26/06 8:26 8.6 42 10/26/06 8:56 8.3

13 10/26/06 8:27 8.6 43 10/26/06 8:57 8.4

14 10/26/06 8:28 8.5 44 10/26/06 8:58 9.1

15 10/26/06 8:29 8.4 45 10/26/06 8:59 9.0

16 10/26/06 8:30 8.5 46 10/26/06 9:00 8.9

17 10/26/06 8:31 8.6 47 10/26/06 9:01 9.2

18 10/26/06 8:32 8.6 48 10/26/06 9:02 9.0

19 10/26/06 8:33 8.9 49 10/26/06 9:03 8.9

20 10/26/06 8:34 9.1 50 10/26/06 9:04 8.6

21 10/26/06 8:35 8.9 51 10/26/06 9:05 8.7

22 10/26/06 8:36 9.0 52 10/26/06 9:06 9.2

23 10/26/06 8:37 9.4 53 10/26/06 9:07 9.3

24 10/26/06 8:38 8.9 54 10/26/06 9:08 8.9

25 10/26/06 8:39 9.0 55 10/26/06 9:09 8.8

26 10/26/06 8:40 8.8 56 10/26/06 9:10 8.7

27 10/26/06 8:41 8.5 57 10/26/06 9:11 9.0

28 10/26/06 8:42 8.5 58 10/26/06 9:12 9.0

29 10/26/06 8:43 8.6 59 10/26/06 9:13 9.2

30 10/26/06 8:44 8.6 60 10/26/06 9:14 8.9

Test Average: 8.71 %

Minimum One Minute Average: 8.20 %

Maximum One Minute Average: 9.40 %

Maximum Six Minute Average: 9.05 %

Visible Emissions Determination from Opacity Monitor

10 
BIG BEND GENERATING STATION

HEAT INPUT CALCULATIONS

Gross Heat Rate, Previous Month (September): 9920 KMBtu/MWh

9.9200E+06 MMBtu/MWh

MegaWatt Hour Integrator Information

Initial Integrator Reading: 937409 MWh

Final Integrator Reading: 940661 MWh

Total: 3252 MWh

Test Time Information

Testing Start Time: 8:15

Testing End Time: 17:15

Total Test Time: 9.00 hours

Calculated Heat Input

Average Unit Load, MW = MWh / hours: 361.3 MW

Heat Input, MMBtu/h = MMBtu/MWh x MW: 3584 mmBtu/hr

Fuel Consumption Calculation

Laboratory Sample ID: AA85469

Btu as received: 11788 Btu/lb

Tons of Fuel Consumed, Tons/hr = (mmBtu/h / Btu/lb) x 500: 152.0 Tons/hour

Unit #2

October 26, 2006

WET-BOTTOM UTILTIY BOILER

11 
5.0 FIGURES

12 
FIGURE 1

EXHAUST STACK

426.5 ’ EL.

BIG BEND GENERATING STATION

PARTICULATE TRAVERSE POINTS

OUTLET

N

PORT LOCATION PLAN

REVISED: 10-Jan-06

CS0W1 (BOILERS 1 & 2) TEST LOCATION

STACK DIAMETERS DOWNSTREAM

FROM DISTURBANCE = 8.74

STACK DIAMETERS UPSTREAM

FROM DISTURBANCE = 2.42

STACK DIAMETER = 29.917 FT. ID.

STACK AREA = 702.952 SQ. FT.

PORT LENGTH = 62 IN.

TRAVERSE

POINT 

1

2

3

% OF

STACK DIAMETER

IN. FROM

STACK WALL

4.4%

14.6%

29.6%

15.80 IN.

52.41 IN.

106.27 IN.

.

499 ’ EL.

165 ’ EL.

261.5 ’

FGD

PRESSURIZED

ANNULUS

72.5 ’

A

B C

D

9 ’ EL.

13 
APPENDIX A

PARTICULATE MATTER CALCULATIONS 
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 5/17

Particulate Test Calculations

Customer: Tampa Electric Company

Facility: Big Bend Station

Sampling Location: CS0W1 - Common Stack 1 - Wet

Unit Under Test: Boiler #2

Operating Conditions: Soot Blowing

Run Number: 1s

Date: October 26, 2006

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.282 inches

Barometric Pressure, Pb: 29.84 "Hg Nozzle Area, An: 0.000434 ft2

Stack Pressure, Ps: 29.83 "Hg Average Orifice Meter, ΔH: 1.197 "H2O

Effective Stack Area, As: 702.952 ft2 Sample Volume, Vm: 37.809 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 79.4 o

F

Gas Analysis: 10.0 % CO2 Average Stack Temp., Ts: 124.2 o

F

9.0 % O2 Average √Δp: 0.502 "H2O

0.0 % CO Condensate Volume, Vlc: 108.0 ml

81.0 % N2 Meter Box Y: 0.999 dimensionless

F-factor, Fd, for fuel: 9780 dscf/MMBtu

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 5.091 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.982 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.121 %

FDA = 1.0 - Bws 0.879 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.96 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.51 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 29.87 ft/second

Qs = vs x As x 60 1259894.6 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 997948.2 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 100.1 %

Data from Laboratory Analysis:

Total Particulate Weight From Laboratory Analysis: 0.01700 grams

Calculated Concentration and Emission Rate Data:

cs = (15.432 x grams) / Vm(std) 0.007 grains/dscf

grains/acf = cs x 17.647 x Ps x (FDA / (Ts + 460) 0.006 grains/acf

C = cs / 7000 1.013E-06 lbs/dscf

ER = C x Fd x (20.9 /(20.9 - %O2) 0.017 lbs/MMBtu
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 5/17

Particulate Test Calculations

Customer: Tampa Electric Company

Facility: Big Bend Station

Sampling Location: CS0W1 - Common Stack 1 - Wet

Unit Under Test: Boiler #2

Operating Conditions: Soot Blowing

Run Number: 2s

Date: October 26, 2006

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.282 inches

Barometric Pressure, Pb: 29.81 "Hg Nozzle Area, An: 0.000434 ft2

Stack Pressure, Ps: 29.80 "Hg Average Orifice Meter, ΔH: 1.148 "H2O

Effective Stack Area, As: 702.952 ft2 Sample Volume, Vm: 37.373 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 82.4 o

F

Gas Analysis: 9.5 % CO2 Average Stack Temp., Ts: 124.0 o

F

11.0 % O2 Average √Δp: 0.491 "H2O

0.0 % CO Condensate Volume, Vlc: 146.2 ml

79.5 % N2 Meter Box Y: 0.999 dimensionless

F-factor, Fd, for fuel: 9780 dscf/MMBtu

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 6.892 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.312 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.160 %

FDA = 1.0 - Bws 0.840 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.96 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.05 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 29.44 ft/second

Qs = vs x As x 60 1241871.7 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 939910.9 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 104.3 %

Data from Laboratory Analysis:

Total Particulate Weight From Laboratory Analysis: 0.03065 grams

Calculated Concentration and Emission Rate Data:

cs = (15.432 x grams) / Vm(std) 0.013 grains/dscf

grains/acf = cs x 17.647 x Ps x (FDA / (Ts + 460) 0.010 grains/acf

C = cs / 7000 1.861E-06 lbs/dscf

ER = C x Fd x (20.9 /(20.9 - %O2) 0.038 lbs/MMBtu
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 5/17

Particulate Test Calculations

Customer: Tampa Electric Company

Facility: Big Bend Station

Sampling Location: CS0W1 - Common Stack 1 - Wet

Unit Under Test: Boiler #2

Operating Conditions: Soot Blowing

Run Number: 3s

Date: October 26, 2006

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.282 inches

Barometric Pressure, Pb: 29.89 "Hg Nozzle Area, An: 0.000434 ft2

Stack Pressure, Ps: 29.88 "Hg Average Orifice Meter, ΔH: 1.176 "H2O

Effective Stack Area, As: 702.952 ft2 Sample Volume, Vm: 38.190 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 97.8 o

F

Gas Analysis: 10.0 % CO2 Average Stack Temp., Ts: 124.5 o

F

10.5 % O2 Average √Δp: 0.490 "H2O

0.0 % CO Condensate Volume, Vlc: 147.5 ml

79.5 % N2 Meter Box Y: 0.999 dimensionless

F-factor, Fd, for fuel: 9780 dscf/MMBtu

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 6.953 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.167 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.161 %

FDA = 1.0 - Bws 0.839 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 30.02 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.08 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 29.35 ft/second

Qs = vs x As x 60 1237879.0 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 936644.1 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 104.3 %

Data from Laboratory Analysis:

Total Particulate Weight From Laboratory Analysis: 0.02365 grams

Calculated Concentration and Emission Rate Data:

cs = (15.432 x grams) / Vm(std) 0.010 grains/dscf

grains/acf = cs x 17.647 x Ps x (FDA / (Ts + 460) 0.008 grains/acf

C = cs / 7000 1.442E-06 lbs/dscf

ER = C x Fd x (20.9 /(20.9 - %O2) 0.028 lbs/MMBtu
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 5/17

Particulate Test Calculations

Customer: Tampa Electric Company

Facility: Big Bend Station

Sampling Location: CS0W1 - Common Stack 1 - Wet

Unit Under Test: Boiler #2

Operating Conditions: Non-Soot Blowing

Run Number: 1

Date: October 26, 2006

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.282 inches

Barometric Pressure, Pb: 29.76 "Hg Nozzle Area, An: 0.000434 ft2

Stack Pressure, Ps: 29.75 "Hg Average Orifice Meter, ΔH: 1.275 "H2O

Effective Stack Area, As: 702.952 ft2 Sample Volume, Vm: 38.760 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 75.5 o

F

Gas Analysis: 10.0 % CO2 Average Stack Temp., Ts: 122.0 o

F

9.0 % O2 Average √Δp: 0.519 "H2O

0.0 % CO Condensate Volume, Vlc: 96.0 ml

81.0 % N2 Meter Box Y: 0.999 dimensionless

F-factor, Fd, for fuel: 9780 dscf/MMBtu

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 4.525 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 38.094 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.106 %

FDA = 1.0 - Bws 0.894 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.96 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.69 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 30.78 ft/second

Qs = vs x As x 60 1298171.6 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 1046781.9 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 98.3 %

Data from Laboratory Analysis:

Total Particulate Weight From Laboratory Analysis: 0.01815 grams

Calculated Concentration and Emission Rate Data:

cs = (15.432 x grams) / Vm(std) 0.007 grains/dscf

grains/acf = cs x 17.647 x Ps x (FDA / (Ts + 460) 0.006 grains/acf

C = cs / 7000 1.050E-06 lbs/dscf

ER = C x Fd x (20.9 /(20.9 - %O2) 0.018 lbs/MMBtu
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 5/17

Particulate Test Calculations

Customer: Tampa Electric Company

Facility: Big Bend Station

Sampling Location: CS0W1 - Common Stack 1 - Wet

Unit Under Test: Boiler #2

Operating Conditions: Non-Soot Blowing

Run Number: 2

Date: October 26, 2006

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.282 inches

Barometric Pressure, Pb: 29.82 "Hg Nozzle Area, An: 0.000434 ft2

Stack Pressure, Ps: 29.81 "Hg Average Orifice Meter, ΔH: 1.169 "H2O

Effective Stack Area, As: 702.952 ft2 Sample Volume, Vm: 37.415 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 79.2 o

F

Gas Analysis: 9.5 % CO2 Average Stack Temp., Ts: 123.8 o

F

10.5 % O2 Average √Δp: 0.496 "H2O

0.0 % CO Condensate Volume, Vlc: 143.0 ml

80.0 % N2 Meter Box Y: 0.999 dimensionless

F-factor, Fd, for fuel: 9780 dscf/MMBtu

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 6.741 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.586 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.156 %

FDA = 1.0 - Bws 0.844 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.94 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.08 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 29.77 ft/second

Qs = vs x As x 60 1255417.7 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 955294.1 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 103.4 %

Data from Laboratory Analysis:

Total Particulate Weight From Laboratory Analysis: 0.01415 grams

Calculated Concentration and Emission Rate Data:

cs = (15.432 x grams) / Vm(std) 0.006 grains/dscf

grains/acf = cs x 17.647 x Ps x (FDA / (Ts + 460) 0.005 grains/acf

C = cs / 7000 8.526E-07 lbs/dscf

ER = C x Fd x (20.9 /(20.9 - %O2) 0.017 lbs/MMBtu
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 5/17

Particulate Test Calculations

Customer: Tampa Electric Company

Facility: Big Bend Station

Sampling Location: CS0W1 - Common Stack 1 - Wet

Unit Under Test: Boiler #2

Operating Conditions: Non-Soot Blowing

Run Number: 3

Date: October 26, 2006

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.282 inches

Barometric Pressure, Pb: 29.89 "Hg Nozzle Area, An: 0.000434 ft2

Stack Pressure, Ps: 29.88 "Hg Average Orifice Meter, ΔH: 1.169 "H2O

Effective Stack Area, As: 702.952 ft2 Sample Volume, Vm: 37.492 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 79.2 o

F

Gas Analysis: 9.5 % CO2 Average Stack Temp., Ts: 123.8 o

F

10.5 % O2 Average √Δp: 0.496 "H2O

0.0 % CO Condensate Volume, Vlc: 143.0 ml

80.0 % N2 Meter Box Y: 0.999 dimensionless

F-factor, Fd, for fuel: 9780 dscf/MMBtu

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 6.741 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.747 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.155 %

FDA = 1.0 - Bws 0.845 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.94 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 28.09 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 29.73 ft/second

Qs = vs x As x 60 1253792.6 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 956950.7 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 103.7 %

Data from Laboratory Analysis:

Total Particulate Weight From Laboratory Analysis: 0.01515 grams

Calculated Concentration and Emission Rate Data:

cs = (15.432 x grams) / Vm(std) 0.0064 grains/dscf

grains/acf = cs x 17.647 x Ps x (FDA / (Ts + 460) 0.0049 grains/acf

C = cs / 7000 9.089E-07 lbs/dscf

ER = C x Fd x (20.9 /(20.9 - %O2) 0.018 lbs/MMBtu
APPENDIX B

PARTICULATE MATTER LABORATORY ANALYTICAL DATA 
Customer AIR SERVICES Plant BIG BEND Unit BOILER 2

Method 5-B Stack Test Completion Date 10/26/2006Analyst SS Sample Number AA85469

ACETONE BEAKER 1st weighing Date 11/1/2006 Time 17:35 % RH 41.5%

2nd weighing Date 11/2/2006 Time 17:15 % RH 41.5%

3rd weighing Date 11/3/2006 Time 18:40 % RH 43.0%

4th weighing Date Time % RH

***Blank*** Run 1 Run 2 Run 3 Run 1S Run 2S Run 3S

Acetone Container ID AIR 55 AIR 51 AIR 59 AIR 77 AIR 108 AIR 17 AIR 05

Acetone Rinse Vol.(Va), mls 200.0000 200 200 200 200 200 200

1st Gross Wt., grams 107.4850 107.4772 107.9577 107.5096 107.3071 105.1141 106.8309

2nd Gross Wt., grams 107.4846 107.4761 107.9566 107.5093 104.3066 105.1129 106.8300

3rd Gross Wt., grams 107.4844 107.4759 107.9562 107.5094 104.3062 105.1129 106.8298

4th Gross Wt., grams

Avg. Gross Wt., grams 107.48480 107.47600 107.95640 107.50945 104.30640 105.11290 106.82990

Tare Wt., grams 107.48385 107.47040 107.94685 107.50420 104.30310 105.09725 106.81985

Acetone Blank Wt., mg 0.95 0.95 0.95 0.95 0.95 0.95 0.95

Acetone Particulate Wt., mg 4.65 8.60 4.30 2.35 14.70 9.10

Acetone Residue, mg/g 0.0060

Acetone Blank Criteria OK to subtract acetone blank

 FILTER 1st weighing Date 11/1/2006 Time 17:10 % RH 41.5%

2nd weighing Date 11/2/2006 Time 17:30 % RH 41.5%

3rd weighing Date Time % RH

4th weighing Date Time % RH

Filter/Thimble ID 203043 203041 203030 203037 203038 203033 203039

1st Gross Wt., grams 0.2649 0.2824 0.2840 0.2859 0.2839 0.2842 0.2831

2nd Gross Wt., grams 0.2650 0.2822 0.2841 0.2856 0.2838 0.2841 0.2828

3rd Gross Wt., grams

4th Gross Wt., grams

Avg. Gross Wt., grams 0.26495 0.28230 0.28405 0.28575 0.28385 0.28415 0.28295

Tare Wt., grams 0.26505 0.26880 0.26765 0.27045 0.26920 0.26820 0.26840

Filter Particulate Wt., mg 13.50 16.40 15.30 14.65 15.95 14.55

Difference, milligrams -0.1

Total Sample Particulate Wt., mg 18.15 25.00 19.60 17.00 30.65 23.65

0.01815 0.02500 0.01960 0.01700 0.03065 0.02365

Start Here
APPENDIX C

BOILER/PRECIPITATOR OPERATIONAL DATA




APPENDIX D

PLANT CEMS DAHS PRINTOUTS
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 8:15 50.3 9.5

10/26/2006 8:16 50.3 9.5

10/26/2006 8:17 50.4 9.6

10/26/2006 8:18 50.3 9.5

10/26/2006 8:19 50.2 9.5

10/26/2006 8:20 49.5 9.5

10/26/2006 8:21 49.8 9.6

10/26/2006 8:22 51.1 9.6

10/26/2006 8:23 51.4 9.6

10/26/2006 8:24 50.8 9.6

10/26/2006 8:25 50.8 9.6

10/26/2006 8:26 50.3 9.4

10/26/2006 8:27 50.4 9.5

10/26/2006 8:28 51.6 9.6

10/26/2006 8:29 52.2 9.7

10/26/2006 8:30 50.5 9.6

10/26/2006 8:31 51.1 9.6

10/26/2006 8:32 49.2 9.6

10/26/2006 8:33 50 9.7

10/26/2006 8:34 48.3 9.5

10/26/2006 8:35 48.1 9.6

10/26/2006 8:36 49.3 9.7

10/26/2006 8:37 48.5 9.6

10/26/2006 8:38 49.2 9.6

10/26/2006 8:39 49.2 9.5

10/26/2006 8:40 49.1 9.6

10/26/2006 8:41 50 9.6

10/26/2006 8:42 49 9.6

10/26/2006 8:43 49.5 9.5

10/26/2006 8:44 48.6 9.5

10/26/2006 8:45 48.3 9.6

10/26/2006 8:46 48.3 9.6

10/26/2006 8:47 50.1 9.6

10/26/2006 8:48 49.8 9.6

10/26/2006 8:49 49.2 9.6

Page 1 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 8:50 49.7 9.6

10/26/2006 8:51 48.2 9.6

10/26/2006 8:52 48.2 9.6

10/26/2006 8:53 49.6 9.6

10/26/2006 8:54 49.4 9.5

10/26/2006 8:55 49.8 9.5

10/26/2006 8:56 49.9 9.6

10/26/2006 8:57 50.1 9.6

10/26/2006 8:58 50 9.6

10/26/2006 8:59 49.6 9.6

10/26/2006 9:00 47.9 9.7

10/26/2006 9:01 48.2 9.7

10/26/2006 9:02 48.1 9.7

10/26/2006 9:03 46.9 9.6

10/26/2006 9:04 47.5 9.6

10/26/2006 9:05 47.5 9.6

10/26/2006 9:06 46.9 9.5

10/26/2006 9:07 46.5 9.4

10/26/2006 9:08 47.4 9.5

10/26/2006 9:09 48.3 9.6

10/26/2006 9:10 48.6 9.6

10/26/2006 9:11 49.4 9.6

10/26/2006 9:12 49.6 9.5

10/26/2006 9:13 49.9 9.5

10/26/2006 9:14 51.3 9.6

10/26/2006 9:15 52.5 9.8

10/26/2006 9:16 50.1 9.6

10/26/2006 9:17 49.6 9.5

10/26/2006 9:18 49.6 9.5

10/26/2006 9:19 50.9 9.7

10/26/2006 9:20 51.8 9.7

10/26/2006 9:21 50.8 9.6

10/26/2006 9:22 51.7 9.7

10/26/2006 9:23 51 9.7

10/26/2006 9:24 50.9 9.6

10/26/2006 9:25 50 9.5

10/26/2006 9:26 50.6 9.7

Page 2 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 9:27 50.6 9.7

10/26/2006 9:28 50.1 9.7

10/26/2006 9:29 49.8 9.6

10/26/2006 9:30 48.3 9.6

10/26/2006 9:31 48.2 9.6

10/26/2006 9:32 49.8 9.6

10/26/2006 9:33 51.2 9.8

10/26/2006 9:34 54.2 9.9

10/26/2006 9:35 53.9 9.9

10/26/2006 9:36 53.7 9.8

10/26/2006 9:37 53 9.8

10/26/2006 9:38 52.6 9.7

10/26/2006 9:39 53.5 9.7

10/26/2006 9:40 52.5 9.7

10/26/2006 9:41 53.6 9.7

10/26/2006 9:42 53.4 9.7

10/26/2006 9:43 53.2 9.8

10/26/2006 9:44 55.8 9.9

10/26/2006 9:45 55 9.9

10/26/2006 9:46 53.1 9.8

10/26/2006 9:47 53.4 9.8

10/26/2006 9:48 53.5 9.8

10/26/2006 9:49 52.1 9.9

10/26/2006 9:50 53.4 9.8

10/26/2006 9:51 53.2 9.8

10/26/2006 9:52 51.4 9.8

10/26/2006 9:53 50.1 9.8

10/26/2006 9:54 49.4 9.8

10/26/2006 9:55 50.5 9.9

10/26/2006 9:56 53.3 10

10/26/2006 9:57 53.2 10

10/26/2006 9:58 51.8 9.9

10/26/2006 9:59 52.1 9.8

10/26/2006 10:00 51.3 9.8

10/26/2006 10:01 51.5 9.8

10/26/2006 10:02 52.8 9.9

10/26/2006 10:03 53.8 9.9

Page 3 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 10:04 56.6 9.9

10/26/2006 10:05 54.6 9.8

10/26/2006 10:06 53.8 9.7

10/26/2006 10:07 53.1 9.8

10/26/2006 10:08 56.3 9.9

10/26/2006 10:09 56.4 10

10/26/2006 10:10 56.1 10

10/26/2006 10:11 55.6 9.9

10/26/2006 10:12 57.4 10

10/26/2006 10:13 56.4 10

10/26/2006 10:14 56.3 9.9

10/26/2006 10:15 54.5 9.8

10/26/2006 10:16 55 10

10/26/2006 10:17 54.1 10

10/26/2006 10:18 53.9 9.9

10/26/2006 10:19 53.6 9.9

10/26/2006 10:20 54.8 10

10/26/2006 10:21 54.3 10

10/26/2006 10:22 55.7 10

10/26/2006 10:23 57.1 10

10/26/2006 10:24 56.8 10

10/26/2006 10:25 55.7 9.9

10/26/2006 10:26 56.5 9.8

10/26/2006 10:27 55.6 9.9

10/26/2006 10:28 54.6 9.8

10/26/2006 10:29 55.6 9.7

10/26/2006 10:30 55.8 9.8

10/26/2006 10:31 57.3 10

10/26/2006 10:32 59.2 10

10/26/2006 10:33 59 10

10/26/2006 10:34 60.3 9.9

10/26/2006 10:35 59.7 9.9

10/26/2006 10:36 58.6 9.8

10/26/2006 10:37 59.1 9.9

10/26/2006 10:38 59.6 10

10/26/2006 10:39 57.5 9.9

10/26/2006 10:40 55.2 9.9

Page 4 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 10:41 54.4 9.9

10/26/2006 10:42 54.2 9.9

10/26/2006 10:43 56.8 10

10/26/2006 10:44 56.5 9.9

10/26/2006 10:45 54.9 9.9

10/26/2006 10:46 55 9.8

10/26/2006 10:47 55 9.8

10/26/2006 10:48 56 9.8

10/26/2006 10:49 55.8 9.8

10/26/2006 10:50 55.9 9.8

10/26/2006 10:51 56.4 9.9

10/26/2006 10:52 56.6 9.9

10/26/2006 10:53 58.3 9.9

10/26/2006 10:54 57.7 9.9

10/26/2006 10:55 57 9.8

10/26/2006 10:56 58.1 9.9

10/26/2006 10:57 56.8 9.9

10/26/2006 10:58 58.8 10.1

10/26/2006 10:59 59.4 10

10/26/2006 11:00 56.9 9.8

10/26/2006 11:01 57.4 9.8

10/26/2006 11:02 56.8 9.9

10/26/2006 11:03 55.5 9.8

10/26/2006 11:04 54.1 9.9

10/26/2006 11:05 57.5 10

10/26/2006 11:06 54.9 9.9

10/26/2006 11:07 53.9 9.8

10/26/2006 11:08 55 9.7

10/26/2006 11:09 55.1 9.9

10/26/2006 11:10 56.7 10

10/26/2006 11:11 56.9 10.1

10/26/2006 11:12 57.8 9.9

10/26/2006 11:13 57.8 9.8

10/26/2006 11:14 57.5 9.9

10/26/2006 11:15 57.9 9.9

10/26/2006 11:16 57.3 9.9

10/26/2006 11:17 58.3 10

Page 5 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 11:18 57.8 10

10/26/2006 11:19 57.8 9.9

10/26/2006 11:20 58.2 9.9

10/26/2006 11:21 56.5 9.9

10/26/2006 11:22 56.4 9.9

10/26/2006 11:23 57.1 9.9

10/26/2006 11:24 57.4 9.8

10/26/2006 11:25 57.3 9.8

10/26/2006 11:26 56.3 9.7

10/26/2006 11:27 55.6 9.8

10/26/2006 11:28 56.2 9.9

10/26/2006 11:29 55.6 10

10/26/2006 11:30 55.1 10

10/26/2006 11:31 55 10

10/26/2006 11:32 56.4 9.9

10/26/2006 11:33 55 9.9

10/26/2006 11:34 55.8 10

10/26/2006 11:35 55.9 9.9

10/26/2006 11:36 56.1 9.9

10/26/2006 11:37 56.8 9.8

10/26/2006 11:38 56.4 9.8

10/26/2006 11:39 58 9.9

10/26/2006 11:40 59 10

10/26/2006 11:41 58.8 10

10/26/2006 11:42 59.4 10.1

10/26/2006 11:43 60.2 10

10/26/2006 11:44 57.9 9.9

10/26/2006 11:45 58.3 10

10/26/2006 11:46 58.1 10

10/26/2006 11:47 58.5 10

10/26/2006 11:48 59 10

10/26/2006 11:49 58.1 10.1

10/26/2006 11:50 57 10

10/26/2006 11:51 55.6 10

10/26/2006 11:52 56.6 10.1

10/26/2006 11:53 58.3 10.1

10/26/2006 11:54 56.9 10

Page 6 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 11:55 56.8 10

10/26/2006 11:56 57.4 10.1

10/26/2006 11:57 58.6 10.1

10/26/2006 11:58 58.7 10.1

10/26/2006 11:59 57.4 10

10/26/2006 12:00 57.3 10

10/26/2006 12:01 59 10.1

10/26/2006 12:02 58.4 10

10/26/2006 12:03 57.2 10

10/26/2006 12:04 59.1 10.1

10/26/2006 12:05 60 10

10/26/2006 12:06 57.4 10

10/26/2006 12:07 58.6 10.1

10/26/2006 12:08 59.8 10.1

10/26/2006 12:09 59.6 10.1

10/26/2006 12:10 59.6 10.2

10/26/2006 12:11 60.6 10.1

10/26/2006 12:12 58.4 10.1

10/26/2006 12:13 56.8 10.1

10/26/2006 12:14 56.7 10.1

10/26/2006 12:15 56.1 10.1

10/26/2006 12:16 55.1 10

10/26/2006 12:17 55.3 10.1

10/26/2006 12:18 55.1 10.1

10/26/2006 12:19 54.2 10.1

10/26/2006 12:20 55.6 9.9

10/26/2006 12:21 56.6 10.1

10/26/2006 12:22 57.6 10.2

10/26/2006 12:23 58.2 10.1

10/26/2006 12:24 56.9 10

10/26/2006 12:25 58.6 10.1

10/26/2006 12:26 60.5 10.2

10/26/2006 12:27 59 10.1

10/26/2006 12:28 58.7 10.1

10/26/2006 12:29 59.3 10.1

10/26/2006 12:30 59.9 10.1

10/26/2006 12:31 60.1 10.1

Page 7 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 12:32 59.2 10.1

10/26/2006 12:33 60.2 10.1

10/26/2006 12:34 60.8 10.2

10/26/2006 12:35 62.5 10.2

10/26/2006 12:36 61.5 10.1

10/26/2006 12:37 61.1 10.1

10/26/2006 12:38 61.3 10.2

10/26/2006 12:39 60.2 10.2

10/26/2006 12:40 59.8 10.2

10/26/2006 12:41 58 10.1

10/26/2006 12:42 57.6 10.1

10/26/2006 12:43 57.8 10.1

10/26/2006 12:44 57.7 10

10/26/2006 12:45 59.5 10.1

10/26/2006 12:46 59.6 10.2

10/26/2006 12:47 61 10.3

10/26/2006 12:48 61.7 10.3

10/26/2006 12:49 61.6 10.3

10/26/2006 12:50 62.4 10.2

10/26/2006 12:51 62 10.2

10/26/2006 12:52 61.5 10.3

10/26/2006 12:53 62.8 10.2

10/26/2006 12:54 63 10.2

10/26/2006 12:55 61.5 10.1

10/26/2006 12:56 62.7 10.1

10/26/2006 12:57 63.9 10.2

10/26/2006 12:58 64.1 10.2

10/26/2006 12:59 63.8 10.2

10/26/2006 13:00 64.3 10.3

10/26/2006 13:01 65.7 10.3

10/26/2006 13:02 63.8 10.3

10/26/2006 13:03 60.8 10.3

10/26/2006 13:04 58.9 10.3

10/26/2006 13:05 58.2 10.2

10/26/2006 13:06 60.4 10.3

10/26/2006 13:07 60.3 10.4

10/26/2006 13:08 59.2 10.2

Page 8 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 13:09 60 10.3

10/26/2006 13:10 60.4 10.3

10/26/2006 13:11 61.8 10.2

10/26/2006 13:12 60.1 10.1

10/26/2006 13:13 60.2 10.2

10/26/2006 13:14 61.5 10.3

10/26/2006 13:15 62.1 10.4

10/26/2006 13:16 62.2 10.4

10/26/2006 13:17 60.5 10.3

10/26/2006 13:18 60.4 10.2

10/26/2006 13:19 61.4 10.3

10/26/2006 13:20 60.1 10.2

10/26/2006 13:21 60 10.2

10/26/2006 13:22 60.2 10.2

10/26/2006 13:23 59.4 10.2

10/26/2006 13:24 60.2 10.3

10/26/2006 13:25 60.3 10.3

10/26/2006 13:26 59 10.2

10/26/2006 13:27 59.6 10.2

10/26/2006 13:28 59.4 10.3

10/26/2006 13:29 59.7 10.3

10/26/2006 13:30 58.4 10.2

10/26/2006 13:31 58.1 10.2

10/26/2006 13:32 58.1 10.1

10/26/2006 13:33 59.6 10.2

10/26/2006 13:34 58.3 10.2

10/26/2006 13:35 58.6 10.1

10/26/2006 13:36 59.2 10.2

10/26/2006 13:37 59.7 10.1

10/26/2006 13:38 59.4 10

10/26/2006 13:39 61.5 10.2

10/26/2006 13:40 62.8 10.3

10/26/2006 13:41 61.7 10.2

10/26/2006 13:42 62.1 10.2

10/26/2006 13:43 61.7 10.2

10/26/2006 13:44 63.1 10.2

10/26/2006 13:45 61.3 10.2

Page 9 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 13:46 60.7 10.2

10/26/2006 13:47 61.1 10.1

10/26/2006 13:48 58.7 10.1

10/26/2006 13:49 58.6 10.2

10/26/2006 13:50 58.1 10.2

10/26/2006 13:51 55.3 10.1

10/26/2006 13:52 54.7 9.9

10/26/2006 13:53 54.2 10

10/26/2006 13:54 55.4 10.2

10/26/2006 13:55 57.8 10.2

10/26/2006 13:56 56.6 10.2

10/26/2006 13:57 56.5 10.2

10/26/2006 13:58 55.9 10.2

10/26/2006 13:59 56.8 10.3

10/26/2006 14:00 57.5 10.3

10/26/2006 14:01 58.6 10.2

10/26/2006 14:02 57.4 10.1

10/26/2006 14:03 57.4 10.2

10/26/2006 14:04 56.9 10.1

10/26/2006 14:05 58.8 10.2

10/26/2006 14:06 57.5 10.1

10/26/2006 14:07 58.3 10.2

10/26/2006 14:08 60.2 10.2

10/26/2006 14:09 59.8 10.2

10/26/2006 14:10 58.5 10.1

10/26/2006 14:11 57.8 10.1

10/26/2006 14:12 56.1 10.1

10/26/2006 14:13 57.2 10.3

10/26/2006 14:14 58.3 10.4

10/26/2006 14:15 55 10.2

10/26/2006 14:16 55.4 10.2

10/26/2006 14:17 56.3 10.2

10/26/2006 14:18 58.4 10.3

10/26/2006 14:19 58.7 10.2

10/26/2006 14:20 58.6 10.2

10/26/2006 14:21 59.9 10.3

10/26/2006 14:22 58.8 10.2

Page 10 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 14:23 59.7 10.1

10/26/2006 14:24 60.8 10.3

10/26/2006 14:25 59.8 10.2

10/26/2006 14:26 58.6 10.2

10/26/2006 14:27 57.7 10.2

10/26/2006 14:28 58.9 10.2

10/26/2006 14:29 59.1 10.2

10/26/2006 14:30 59 10.1

10/26/2006 14:31 60 10.2

10/26/2006 14:32 62.1 10.3

10/26/2006 14:33 59.1 10.2

10/26/2006 14:34 57.1 10.1

10/26/2006 14:35 57 10.2

10/26/2006 14:36 56.8 10.2

10/26/2006 14:37 56.2 10.2

10/26/2006 14:38 54.9 10.2

10/26/2006 14:39 56.7 10.3

10/26/2006 14:40 57.9 10.3

10/26/2006 14:41 58.1 10.2

10/26/2006 14:42 56.3 10.2

10/26/2006 14:43 55.8 10.1

10/26/2006 14:44 56.8 10.2

10/26/2006 14:45 55.9 10.1

10/26/2006 14:46 56.2 10

10/26/2006 14:47 57.4 10

10/26/2006 14:48 57.6 10.2

10/26/2006 14:49 57.1 10.2

10/26/2006 14:50 55.4 10.1

10/26/2006 14:51 56.4 10.1

10/26/2006 14:52 56.2 10.1

10/26/2006 14:53 57.1 10.1

10/26/2006 14:54 56 10.2

10/26/2006 14:55 55.1 10.2

10/26/2006 14:56 53.4 10.1

10/26/2006 14:57 52.5 10

10/26/2006 14:58 52.8 10

10/26/2006 14:59 54.4 10.1

Page 11 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 15:00 53.6 10.1

10/26/2006 15:01 53.9 10

10/26/2006 15:02 55.3 10.1

10/26/2006 15:03 56 10.1

10/26/2006 15:04 55.4 10.1

10/26/2006 15:05 54 10.1

10/26/2006 15:06 54.4 10.1

10/26/2006 15:07 54.7 10.1

10/26/2006 15:08 56.5 10.2

10/26/2006 15:09 55.2 10.2

10/26/2006 15:10 54.7 10

10/26/2006 15:11 55.5 10

10/26/2006 15:12 55.2 10.1

10/26/2006 15:13 56.9 10.1

10/26/2006 15:14 56.6 10.2

10/26/2006 15:15 55.8 10.2

10/26/2006 15:16 56 10.1

10/26/2006 15:17 54.3 10

10/26/2006 15:18 52.2 10

10/26/2006 15:19 52.7 10.1

10/26/2006 15:20 53.2 10.3

10/26/2006 15:26 54.9 9.8

10/26/2006 15:27 54.9 9.8

10/26/2006 15:28 55.8 9.9

10/26/2006 15:29 56.5 9.9

10/26/2006 15:30 52.9 9.8

10/26/2006 15:31 54.5 9.9

10/26/2006 15:32 57.1 10

10/26/2006 15:33 55.4 10.1

10/26/2006 15:34 56.7 10.1

10/26/2006 15:35 56.5 10.1

10/26/2006 15:36 55.2 10.1

10/26/2006 15:37 55.2 10.1

10/26/2006 15:38 54.7 10.1

10/26/2006 15:39 56.4 10.2

10/26/2006 15:40 56.7 10.2

10/26/2006 15:41 55.1 10.1

Page 12 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 15:42 52 10.1

10/26/2006 15:43 52.2 10.1

10/26/2006 15:44 52.2 10.1

10/26/2006 15:45 52 10.2

10/26/2006 15:46 52.2 10.1

10/26/2006 15:47 51.3 10.2

10/26/2006 15:48 52.8 10.3

10/26/2006 15:49 54.5 10.2

10/26/2006 15:50 54 10.2

10/26/2006 15:51 54.5 10.2

10/26/2006 15:52 54.4 10.2

10/26/2006 15:53 55.1 10.1

10/26/2006 15:54 56.8 10.2

10/26/2006 15:55 57.1 10.3

10/26/2006 15:56 56.7 10.2

10/26/2006 15:57 56.2 10.2

10/26/2006 15:58 55.4 10.1

10/26/2006 15:59 56.3 10.3

10/26/2006 16:00 59.3 10.5

10/26/2006 16:01 59.7 10.5

10/26/2006 16:02 59.2 10.5

10/26/2006 16:03 59.6 10.4

10/26/2006 16:04 58.8 10.4

10/26/2006 16:05 58.4 10.5

10/26/2006 16:06 57.6 10.5

10/26/2006 16:07 55.2 10.4

10/26/2006 16:08 54.9 10.2

10/26/2006 16:09 54 10.3

10/26/2006 16:10 54.7 10.4

10/26/2006 16:11 56.3 10.4

10/26/2006 16:12 55.8 10.4

10/26/2006 16:13 54.8 10.3

10/26/2006 16:14 57 10.2

10/26/2006 16:15 55 10.3

10/26/2006 16:16 55.3 10.3

10/26/2006 16:17 56.6 10.4

10/26/2006 16:18 56.5 10.4

Page 13 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 16:19 55 10.3

10/26/2006 16:20 56.2 10.3

10/26/2006 16:21 57.4 10.2

10/26/2006 16:22 58.2 10.2

10/26/2006 16:23 57.1 10.2

10/26/2006 16:24 56.1 10.2

10/26/2006 16:25 57.8 10.3

10/26/2006 16:26 57.8 10.3

10/26/2006 16:27 55.8 10.3

10/26/2006 16:28 55.4 10.2

10/26/2006 16:29 55.7 10.4

10/26/2006 16:30 54.6 10.4

10/26/2006 16:31 54.8 10.4

10/26/2006 16:32 53.6 10.3

10/26/2006 16:33 51.7 10.1

10/26/2006 16:34 52.3 10.2

10/26/2006 16:35 53.7 10.3

10/26/2006 16:36 55.1 10.3

10/26/2006 16:37 56.2 10.4

10/26/2006 16:38 55.4 10.3

10/26/2006 16:39 55.3 10.2

10/26/2006 16:40 54.9 10.1

10/26/2006 16:41 54.7 10

10/26/2006 16:42 55.3 10.1

10/26/2006 16:43 56.9 10.2

10/26/2006 16:44 58.1 10.3

10/26/2006 16:45 56.6 10.2

10/26/2006 16:46 55.5 10.1

10/26/2006 16:47 56.2 10.1

10/26/2006 16:48 58.4 10.2

10/26/2006 16:49 57 10.3

10/26/2006 16:50 55.7 10.1

10/26/2006 16:51 54.7 10.2

10/26/2006 16:52 55.9 10.3

10/26/2006 16:53 54.2 10.3

10/26/2006 16:54 54.2 10.2

10/26/2006 16:55 54.4 10.3

Page 14 of 15
Big Bend Unit 2 Compliance SO2 Data 

Date Time SO21 CO21

10/26/2006 16:56 55.9 10.4

10/26/2006 16:57 56.4 10.4

10/26/2006 16:58 56 10.2

10/26/2006 16:59 54.9 10.2

10/26/2006 17:00 56.1 10.2

10/26/2006 17:01 57.1 10.3

10/26/2006 17:02 57.5 10.3

10/26/2006 17:03 54.6 10.2

10/26/2006 17:04 54.6 10.1

10/26/2006 17:05 54.9 10.1

10/26/2006 17:06 57.3 10.3

10/26/2006 17:07 56.6 10.2

10/26/2006 17:08 56.2 10.2

10/26/2006 17:09 55.2 10.1

10/26/2006 17:10 58 10.2

10/26/2006 17:11 58.1 10.4

10/26/2006 17:12 57.5 10.3

10/26/2006 17:13 56.6 10.3

10/26/2006 17:14 54.6 10.2

10/26/2006 17:15 53.2 10.1

Averages: 55.87 10.02

Note: Data from 15:21 through 15:25

removed from averaqe due to probe

blowback.

Page 15 of 15
Date Time OPACITY2

10/26/2006 9:44 7.9

10/26/2006 9:45 7.5

10/26/2006 9:46 7.3

10/26/2006 9:47 7.4

10/26/2006 9:48 7.3

10/26/2006 9:49 7.5

10/26/2006 9:50 7

10/26/2006 9:51 6.9

10/26/2006 9:52 6.9

10/26/2006 9:53 6.6

10/26/2006 9:54 6.8

10/26/2006 9:55 7.7

10/26/2006 9:56 7.6

10/26/2006 9:57 7.1

10/26/2006 9:58 7.2

10/26/2006 9:59 7.1

10/26/2006 10:00 6.6

10/26/2006 10:01 7.2

10/26/2006 10:02 7.5

10/26/2006 10:03 7.1

10/26/2006 10:04 6.9

10/26/2006 10:05 6.7

10/26/2006 10:06 6.6

10/26/2006 10:07 7.2

10/26/2006 10:08 7.3

10/26/2006 10:09 7.3

10/26/2006 10:10 7.1

10/26/2006 10:11 7.1

10/26/2006 10:12 6.5

10/26/2006 10:13 6.7

10/26/2006 10:14 6.8

10/26/2006 10:15 6.8

10/26/2006 10:16 7.4

10/26/2006 10:17 6.9

10/26/2006 10:18 6.5

10/26/2006 10:19 6.6

10/26/2006 10:20 6.7

10/26/2006 10:21 6.8

10/26/2006 10:22 6.8

10/26/2006 10:23 7.3

10/26/2006 10:24 7.5

10/26/2006 10:25 7

Page 1 of 2
Date Time OPACITY2

10/26/2006 10:26 6.8

10/26/2006 10:27 6.8

10/26/2006 10:28 6.9

10/26/2006 10:29 7

10/26/2006 10:30 7.1

10/26/2006 10:31 7.5

10/26/2006 10:32 7.2

10/26/2006 10:33 7.2

10/26/2006 10:34 7.1

10/26/2006 10:35 7.1

10/26/2006 10:36 7.2

10/26/2006 10:37 7.3

10/26/2006 10:38 7.1

10/26/2006 10:39 7.1

10/26/2006 10:40 7.8

10/26/2006 10:41 7.4

10/26/2006 10:42 8.1

10/26/2006 10:43 8.5

10/26/2006 10:44 7.8

Page 2 of 2
Date Time OPACITY2

10/26/2006 8:15 8.5

10/26/2006 8:16 8.3

10/26/2006 8:17 8.4

10/26/2006 8:18 8.4

10/26/2006 8:19 8.7

10/26/2006 8:20 8.9

10/26/2006 8:21 8.8

10/26/2006 8:22 9

10/26/2006 8:23 8.3

10/26/2006 8:24 8.3

10/26/2006 8:25 8.4

10/26/2006 8:26 8.6

10/26/2006 8:27 8.6

10/26/2006 8:28 8.5

10/26/2006 8:29 8.4

10/26/2006 8:30 8.5

10/26/2006 8:31 8.6

10/26/2006 8:32 8.6

10/26/2006 8:33 8.9

10/26/2006 8:34 9.1

10/26/2006 8:35 8.9

10/26/2006 8:36 9

10/26/2006 8:37 9.4

10/26/2006 8:38 8.9

10/26/2006 8:39 9

10/26/2006 8:40 8.8

10/26/2006 8:41 8.5

10/26/2006 8:42 8.5

10/26/2006 8:43 8.6

10/26/2006 8:44 8.6

10/26/2006 8:45 8.9

10/26/2006 8:46 8.8

10/26/2006 8:47 8.5

10/26/2006 8:48 8.8

10/26/2006 8:49 8.7

10/26/2006 8:50 8.6

10/26/2006 8:51 8.3

10/26/2006 8:52 8.2

10/26/2006 8:53 8.3

10/26/2006 8:54 8.4

10/26/2006 8:55 8.2

10/26/2006 8:56 8.3

Page 1 of 2
Date Time OPACITY2

10/26/2006 8:57 8.4

10/26/2006 8:58 9.1

10/26/2006 8:59 9

10/26/2006 9:00 8.9

10/26/2006 9:01 9.2

10/26/2006 9:02 9

10/26/2006 9:03 8.9

10/26/2006 9:04 8.6

10/26/2006 9:05 8.7

10/26/2006 9:06 9.2

10/26/2006 9:07 9.3

10/26/2006 9:08 8.9

10/26/2006 9:09 8.8

10/26/2006 9:10 8.7

10/26/2006 9:11 9

10/26/2006 9:12 9

10/26/2006 9:13 9.2

10/26/2006 9:14 8.9

10/26/2006 9:15 8.7

Page 2 of 2
APPENDIX E

FUEL ANALYSIS 
Laboratory Services

5012 Causeway Blvd * Tampa Fl. 33619 

 Ph (813) 630-7378 * Fax (813) 630-7360 * DOH #E54272

Report For: 11/14/2006

Location Code: TE_BB_2_COMP_CO

Location Description:

Sample Collector:

Sample Collection Date

Lab Submittal Date:

Sample Information

Big Bend 2 Compliance 10/26/2006

10/30/2006

ASG

Report Date:

Laboratory ID: AA85469

Laboratory Results

Coal Analysis - As Received Result Units

Lower

Limit

Upper

Limit Violation

Ash, as Received 8.59 %

BTU, as Received 11788 BTU/Lb

Sulfur, as Received 2.85 %

Coal Analysis - Dry Basis Result Units

Lower

Limit

Upper

Limit Violation

Ash, Dry Basis 9.60 %

BTU, Dry Basis 13172 BTU/Lb.

Sulfur, Dry Basis 3.18 %

Coal Analysis - Miscellaneous Result Units

Lower

Limit

Upper

Limit Violation

BTU, Moisture-Ash Free 14571 BTU/Lb.

Pounds SO2 / Million BTU 4.59 Lbs. SO2/MMBTU

Total Moisture 10.51 %

Comments

Robert Dorey,

Manager, Laboratory Services

Report Number: -111406- 09 AA85469 Page 1 of 1 "Coal Report"
APPENDIX F

FIELD DATA SHEETS 






APPENDIX G

SAMPLING EQUIPMENT CALIBRATIONS 
SUMMARY OF EQUIPMENT CALIBRATIONS

Big Bend Unit #2

EQUIPMENT CAL DATE METHOD RESULTS

CONSOLE (MB 07) USEPA RM 5

INITIAL 10/03/06 (ORIFICE) 0.999

POST TEST 10/09/06 0.982

NOZZLE SN19

INITIAL 10/02/06 CALIPER 0.282

POST TEST 11/01/06 MEASUREMENTS 0.283

PYROMETER (PY 09) 10/03/06 ASTM THERMOMETER + 2o

 F

PITOT TUBE (PT 05) 10/03/06 USEPA RM 2 Cp = 0.84

BAROMETER (BR 07) 10/02/06 NWS COMPARISON + 0.01" Hg
Environmental Services

Air Services Group

Blue Team

Manufacturer: Thermo Anderson Calibration Date:

Model Number:MST-C1 Barometric Pressure: 30.15 "Hg

Instrument Code Number: ^MB07 Theoretical Critical Vacuum: 14.22 "Hg

LabWorks Sample Number: Calibrated By:

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

0.60 15 356.984 363.887 6.903 79 77 79 77

1.10 15 347.782 356.984 9.202 81 78 80 78

1.90 15 335.841 347.782 11.941 81 78 83 78

3.50 15 319.720 335.841 16.121 80 75 88 78

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

48 0.3483 22.0 72 72 72.0

55 0.4660 21.0 72 72 72.0

63 0.5971 19.0 72 72 72.0

73 0.8177 16.5 72 72 72.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

6.834 6.829 6.831 0.999 0.000 1.610 -0.060

9.100 9.137 9.140 1.004 0.005 1.645 -0.025

11.815 11.708 11.711 0.991 -0.008 1.729 0.058

16.006 16.033 16.038 1.002 0.003 1.697 0.027

Averages: 0.999 1.670

Review/Approval: 5-Oct-06

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

Quarterly Calibration

10/3/2006

JAV

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.

IMPORTANT

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice Readings

Ambient Temperatures

CALCULATED DATA

Critical Orifice
Environmental Services

Air Services Group

Manufacturer: Thermo Calibration Date:

Model Number:MST Barometric Pressure: 30.15 "Hg

Instrument Code Number: MB07 Theoretical Critical Vacuum: 14.22 "Hg

LabWorks Sample Number: Calibrated By:

Associated Test: Team: BLUE

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

1.1 10 640.400 646.530 6.130 72 72 74 72

1.1 10 646.530 652.600 6.070 74 72 75 73

1.1 10 652.600 658.750 6.150 74 73 77 74

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

55 0.4592 20.5 72 72 72.0

55 0.4592 20.5 72 72 72.0

55 0.4592 20.5 72 72 72.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

6.139 6.003 6.004 0.978 -0.004 1.716 0.003

6.067 6.003 6.004 0.989 0.008 1.713 0.000

6.136 6.003 6.004 0.978 -0.004 1.709 -0.003

Averages: 0.982 1.713

Prior Y: 0.999

% Difference: 1.72%

Review/Approval: Date:

Big Bend CS001W

IMPORTANT

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.

Ambient Temperatures

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

Critical Orifice Readings

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

GDB

11/9/2006

POST - TEST CALIBRATION CHECK

10-Nov-06

CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice
Environmental Services

Air Services Group

QUARTERLY NOZZLE CALIBRATIONS

Shared Resource

STEEL NOZZLE SET

Calibration Date: 10/2/2006 Responsible Party: SEG

Nozzle Nozzle Diameter, Dn (cm) Maximum Average

I.D. D1 D2 D3 Difference, " Dn, inches

^SN01 0.296 0.294 0.290 0.002 0.115

^SN04 0.320 0.320 0.320 0.000 0.126

^SN05 0.380 0.380 0.378 0.001 0.149

^SN06 0.500 0.496 0.500 0.002 0.196

^SN09 0.695 0.689 0.690 0.002 0.272

^SN10 0.755 0.750 0.755 0.002 0.297

^SN12 0.985 0.985 0.983 0.001 0.388

^SN15 0.420 0.420 0.420 0.000 0.165

^SN16 0.504 0.505 0.505 0.000 0.199

^SN19 0.717 0.714 0.715 0.001 0.282

^SN22 0.932 0.930 0.934 0.002 0.367

^SN30 0.795 0.792 0.795 0.001 0.313

^SN36 0.480 0.477 0.477 0.001 0.188

^SN37 0.535 0.534 0.532 0.001 0.210

^SN38 0.635 0.640 0.640 0.002 0.251

^SN46 0.482 0.485 0.483 0.001 0.190

^SN47 0.515 0.516 0.516 0.000 0.203

^SN48 0.645 0.640 0.640 0.002 0.253

^SN50 0.788 0.790 0.791 0.001 0.311

^SN58 0.619 0.611 0.615 0.003 0.242

^SN68 0.630 0.625 0.632 0.003 0.248

^SN69 0.950 0.950 0.950 0.000 0.374

^SN70 1.565 1.565 1.565 0.000 0.616

^SN71 1.558 1.560 1.560 0.001 0.614

^SN72 0.955 0.953 0.950 0.002 0.375

^SN73 1.277 1.280 1.280 0.001 0.504

^SN74 1.245 1.240 1.245 0.002 0.490

Data Notations: All micometer readings are converted from cm to inches by multiplying by

0.393700787. Maximum Difference must be < 0.004".

QA/QC Review by: 5-Oct-06
Environmental Services

Air Services Group

POST TEST NOZZLE CALIBRATION 

Shared Resource

Calibration Date: 11/1/2006

Calibration Personnel: Jorge A. Varino

Test Designation:

Nozzle Nozzle Diameter, Dn (cm) Maximum Average

Identifier D1 D2 D3 Difference, " Dn, inches

SN19 0.720 0.720 0.717 0.001 0.283

Data Notations: All micometer readings are converted from cm to inches by multiplying by

0.393700787. Maximum Difference must be < 0.004".

Quarterly (pre-test) value for nozzle ID SN19 was 0.282

Difference (Pre-test/Post-test) is: -0.001

QA/QC Review by: 1-Nov-06
Environmental Services

Air Services Group

Pyrometer Calibration

Blue Team

Pyrometer Under Test

Pyrometer Number: ^PY09

Labworks Sample # 0

Calibration Date: 10/2/2006

Calibrator Information

Calibrator Type/Manufacturer: Hart Scientific

Calibrator Serial Number: AOA024

Date of Last Calibration: 7/11/2006

Calibration Personnel (Typed and Signature): JAV

Calibration Data

Calibration Reference Pyrometer

Point Temperature Indication Difference

1 400 399 1

2 212 213 -1

3 32 33 -1

Reference temperatures must encompass the expected range of measurement. These three points

should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit.

Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration

Point Difference

1 Pass

2 Pass

3 Pass

Reviewer: 5-Oct-06
Environmental Services

Air Services Group

_ _

s

PITOT TUBE CALIBRATION

DATA SHEET

Pitot Tube ID # PT05

Calibration Date 10/3/2006 Operating Quarter/Year: Red Team

Openings Damaged? ___ Y __ N Repaired? ___ Y ___ N ___ N/A

Labworks #: 0

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 2 degrees Pass Dt 0.48 < Dt > 0.95 cm

α 2 0.8 degrees Pass α < 10 degrees

β 1 2.1 degrees Pass (α1 measured across top impact openings)

β 2 3.1 degrees Pass (α2 measured across bottom impact openings)

β1 < 5 degrees (alongside top impact openings)

Gamma, Theta, Α, Ζ, and W Determination β2 < 5 degrees (alongside bottom impact openings)

ψ 0.3 degrees Ζ < 0.32 cm (Αsinψ)

Α 2.31 cm W < 0.08 cm (Asinο)

Ζ 0.012 cm Pass Α distance between tips

ο angle of plane on side of pitots

ο 0.1 degrees ψ angle between tips

W 0.004 cm Pass

NOTES

All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, 

Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement

details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems:

Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.

Comments: REMOVABLE

Calibrated by:

Quality Assurance Review / Approval: 16-Oct-06
Environmental Services

Air Services Group

BAROMETER CALIBRATION

Blue Team

Instrument Number: ^BR04

Calibration Date: 10/2/2006

Calibration Personnel: JAV

Labworks #:

Barometer Reading Reference Reading Difference

Time Inches Mercury Inches Mercury "Hg

11:00 30.25 30.18 0.07

13:00 30.2 30.15 0.05

14:50 30.2 30.12 0.08

Average Difference: 0.07

Note: Barometric readings must agree within ± 0.1 "Hg.

Current Reference is National Weather Service, TIA.

Current Conditions at Tampa International Airport

Comments (Note any adjustments):

QA/QC Review by: Date: 5-Oct-06
APPENDIX H

CHAIN OF CUSTODY 


APPENDIX I

TEST PARTICIPANTS 
TEST PARTICIPANTS

ENVIRONMENTAL SERVICES 

AIR SERVICES GROUP

Test Team

Scott Given Associate Technician 

Charles Dufeny Environmental Technician 

Jorge Varino Environmental Technician, Test Team Lead 

Process Data

Curtis Seebaran Engineer, Big Bend Station 

Raymond A. McDarby Senior Environmental Technician 

Fuel Analysis

Patrece Jackson Environmental Technician 

Sample Analysis

Sam Soth Environmental Technician 

Report Preparation

Raymond A. McDarby Senior Environmental Technician 

Test Coordination

Curtis Seebaran Engineer, Big Bend Station