FAQ
    
    AGREEMENT STATES
    
    Facility Locator
    
    What's New
    
    Site Help
    
    Index A-Z
    
    Contact Us
    
    Email Updates
      
      
      
      
       
      Report a Safety Concern
                  Search
        Nuclear Reactors
  
  Power Reactors
Research & Test ReactorsOperating Reactors
New ReactorsOperator Licensing
Research ActivitiesNuclear Reactor Quick LinksNuclear Materials
  
  Types of Nuclear Materials
Fuel Cycle Facilities
Medical, Industrial, & Academic UsesUranium Recovery
Materials TransportationMaterials Environmental Reviews
National Materials ProgramNuclear Materials Quick LinksRadioactive Waste
  
  Decommissioning of Nuclear Facilities
Low-Level Waste
Waste Incidental to Reprocessing
High-Level WasteUranium Mill Tailings
Low-Level Waste Disposal
High-Level Waste DisposalStorage of Spent Nuclear Fuel
Transportation of Spent Nuclear Fuel
Research ActivitiesRadioactive Waste Quick LinksNuclear Security
  
  Domestic Safeguards
Information Security
Radioactive Material SecurityRequired Reporting for Clearance Holders
Insider Threat Program for Licensees
CybersecurityCriminal History & Firearms Checks
Contact UsPublic Meetings & Involvement
  
  The NRC Approach to Open Government
About Meetings Open to the Public
Conferences & SymposiaDocuments for Comment
NRC Rules and Petitions
Facilitating Stakeholder InvolvementNRC Information Quality Guidelines
Subscribe to E-mail UpdatesCommission Schedule
Public Meeting ScheduleAdjudications (Hearings)
Adjudicatory SubmissionsNRC Library
  
  Basic References
Document Collections
ADAMS Public Documents
Public Document Room
LSN LibraryFOIA & Privacy Act
Photos & Videos
Records Management
Training CoursesFAQ Index
Get Copies of Documents
Withholding of Sensitive Information
Controlled Unclassified Information Program (CUI)Electronic Hearing DocketAbout NRC
  
  The Commission
Organization & Functions
Governing Legislation
Plans, Budget, & Performance
Locations
History
Values
Direction-Setting & Policymaking
Research Activities
Radiation ProtectionFire Protection
Safety Culture
How We Regulate
Emergency Preparedness & Response
Public Affairs
Congressional Affairs
Enforcement
International Programs
State & Tribal ProgramsAlternative Dispute Resolution Programs
Privacy Program
Civil Rights Program
Contact Us
Career Opportunities
Contracting Opportunities
Small Businesses
Grant Opportunities
Generic SchedulesOther Links
  
  FAQ
Glossary
Facility Locator
What's NewSite Help
Index A-Z
Contact Us
Email UpdatesNRC Facebook
NRC Twitter Feed
NRC Linkedin
NRC Youtube Channel
NRC Flickr Gallery
NRC Blog Archived
NRC Email Subscriptions - GovDelivery Home
          NRC Library  Document Collections  NUREG-Series Publications  Publications Prepared by NRC ContractorsSteam Generator Tube Integrity Program/Steam Generator Group Project: Final Project Summary Report (NUREG/CR-5117)

On this page: Publication Information AbstractDownload complete document NUREG/CR-5117 (PDF - 12.92 MB)Publication Information **Manuscript Completed:** April 1990**Date Published:** May 1990 **Prepared by:** R.J. Kurtz, R.A. Clark, E.R. Bradley, W.M. Bowen, P.G. Doctor, R.H. Ferris, F.A. Simonen Pacific Northwest Laboratory Richland, WA 99352 **Prepared for:** Division of Engineering Office of Nuclear Regulatory Research U.S. Nuclear Regulatory Commission Washington, DC 20555 NRC FIN B2097 Availability Notice Abstract The Steam Generator Tube Integrity Program/Steam Generator, Group Project was a three-phase program conducted for the U.S. Nuclear Regulatory Commission (NRC) by Pacific Northwest Laboratory.(a) The main goal of the program was to provide the NRC with validated information on the reliability of nondestructive examination techniques to detect and size flaws in steam generator tubing and to determine the remaining integrity of service-degraded tubing. The information was used to determine the effectiveness of NRC Regulatory Guides 1.83, Rev. 1, and 1.121 to 1) define the frequency, extent and procedure for conducting nondestructive inservice inspections of steam generator tubing, and 2) define plugging limits of service-degraded tubing under normal operating and accident loading conditions. The program was performed in three phases. The first phase involved burst and collapse tests and single-frequency eddy-current (EC) examinations of typical steam generator tubing with precision machined flaws. The goal of Phase I was to develop empirical models of remaining tube integrity as a function of flaw type and size, and to determine the capability of EC inspection methods to detect and size tube degradation. In Phase II, a smaller number of specimens with the same flaw types were investigated, but tube specimens were degraded by chemical means rather than machining methods. This approach was used to better simulate the irregular geometry of service-induced degradation. In the final phase of the program, the retired-from-service Surry 2A Steam Generator was used as a test bed to investigate the reliability of inservice EC inspection equipment, personnel, and procedures, and as a source of service-degraded tubes for further validating the empirical equations of remaining tube integrity. In addition, the generator was also used to study the effects of primary-side chemical decontamination, the effectiveness of secondary-side visual examinations, characterizationý of tubesheet crevice corrosion products and sludge pile composition, and demonstrations of tube unplugging and repair techniques. This portion of the program also included participation by three foreign countries. This report summarizes the findings of more than eleven years of research activity on steam generator tube integrity and inspection issues. The results of the Phase I pressure tests on mechanically-flawed steam generator tubing are presented. In addition, the laboratory EC sizing results on those tubes are summarized. A discussion of Phase II pressure test results on chemically-degraded tubes is given, along with a brief overview of leak-rate data for tubes with laboratory-produced axial or circumferential stress-corrosion cracks (SCC). Comparisons with a simple analytical leak rate model are discussed. Laboratory EC estimates of flaw size in Phase II specimens are described. To supplement the laboratory EC data and obtain an estimate of EC reliability to detect and size SCC, results of a mini-round robin involving several firms that routinely perform field inservice inspections are presented. A major portion of the report is devoted to summarizing and integrating the results from the more than six years of research on the Surry 2A Steam Generator. A brief description of the acquisition, transportation and placement of the steam generator into a specially built examination facility is given. Prior to performing extensive nondestructive examination (NDE) of the generator tubing, dilute chemical decontamination of the channel head and removal of plugs placed during service was performed. To determine a post-service baseline condition of the generator, two nearly 100% multifrequency EC inspections were performed along with visual inspections from the secondary side. From these inspections, a subset of 320 tubes was selected for round robin inspection and development of the data base on EC inspection reliability. A description of the four round robins conducted is provided. A summary of the methods used to remove more than 550 tube segments to validate the round robin inspection data is given. Results from the metallurgical and visual examinations of these specimens are discussed. Burst tests of removed-from-generator specimens with pitting/wastage-type degradation are presented and correlated with the empirical models of remaining tube integrity. Statistical analyses of the combined metallurgical and EC data to determine probability of detection and sizing accuracy are reported along with a discussion of the factors which influenced the results. Analyses and Monte Carlo simulations used to evaluate and compare various sampling plans for inservice inspection are described. Finally, recommendations for improved inservice inspection and maintenance of steam generator tube integrity are given. (a) Pacific Northwest Laboratory is operated for the U.S. Department of Energy by Battelle Memorial Institute under Contract DE-ACO6-76RLO 1830. 
      
      Page Last Reviewed/Updated Wednesday, March 24, 2021  Home
NEWS RELEASES

EVENT REPORTS

ADAMS

OPEN GOV

DIGITAL GOVERNMENT

THE STUDENT CORNER

PHOTOS & VIDEOS

FOR DEVELOPERS
        About Us
STRATEGIC PLAN

BUDGET & PERFORMANCE

AGENCY FINANCIAL REPORT

LICENSE FEES

HISTORY OF THE NRC

CAREER OPPORTUNITIES

NRC ETHICS

AGENCY STATUS

CONTACT US
        Popular Documents
INFO DIGEST

FACT SHEETS & BROCHURES

FORMS

ELECTRONIC SUBMITTALS APPLICATION

ADJUDICATORY SUBMISSIONS

NRC REPORTS - NUREG

NRC REGULATIONS - 10-CFR

INSPECTION REPORTS

PLAIN WRITING

ENFORCEMENT ACTIONS

RULEMAKING

GLOSSARY
        Stay Connected
    
    
    
    
    United States Nuclear Regulatory Commission
    
    
    
    
    Regulations.gov

USA.gov

FOIA

Whistleblower Protection

No Fear EEO

Inspector General

Site Map

Accessibility

Privacy Policy

Site Disclaimer

For Employees