Stage II Final Amendments Redline/Strikeout opy ~ 2-01-08 

310 CMR 7.00 Definitions 

Isolate shall meanmeans, for the purposes of 310 CMR 7.24(6), to take out of service ef-one or 

more components of a Stage ll system so that the remainder of the Stage ll system operates as 

required by the terms and conditions of the system's currently applicable Executive Order. 

Minor Modification shall meanmeans, for the purposes of310 CMR 7.24(6), the re-installation, 

repair or replacement of one or more Stage II System components that is not substantial, 

including, but not limited to: less than 50% of the motor vehicle fuel dispensers (e.g., 1 of 4 

dispensers); a central vacuum unit of a Healy 400 ORVR nozzle system or Healy 600 nozzle 

system; ball float extractor valve housings; dispenser mounted vapor pumps; or "screw-on" spill 

or dry break buckets. If the re-installation, repair or replacement of Stage II System components 

occurs at a motor vehicle fuel dispensing facility with two or less dispensers, the re-installation, 

repair or replacement of only one of the motor vehicle fuel dispensers shall be a Minor 

Modification. 

Routine Maintenance sl1all meanmeans, for the purposes of 310 CMR 7.24(6), the regular reinstallation, repair or replacement of one or more Stage II System components including, but not 

limited to: hoses; nozzles; breakaways; swivels; hose retractors; bucket plow rings; "slip-on" 

spill or dry break buckets; "0" rings and seals; submersible pumps or suction pipes; fill adaptors; 

fill tubes; vapor adaptors; fill and vapor caps; drain valves; monitor caps; or riser caps. 

Substantial Modification shall meanmeans, for the purposes of 310 CMR 7.24(6), the reinstallation, repair or replacement of one or more Stage II System components including, but not 

limited to: 50% or more of the motor vehicle fuel dispensers (e.g., 2 of 4 dispensers); the 

replacement of one type of Stage II system with another type (e.g., replacement of a balance 

system with a vacuum assist system, or a Healy 400 ORVR nozzle system or Healy 600 nozzle 

system with a Healy VP-1 000 system); or the re-installation, repair or replacement of Stage II 

System components requiring excavation below a shear valve or tank pad (e.g., vapor return 

piping, vent piping, vapor space tie bar, two-point or coaxial Stage I systems; or motor vehicle 

fuel storage tanks). If there-installation, repair or replacement of one or more Stage II System 

components occurs at a motor vehicle fuel dispensing facility with two or fewer dispensers, the 

re-installation, repair or replacement of all motor vehicle fuel dispensers shall be a Substantial 

Modification. 

310 CMR 7.24(6) U DISPENSING.QF MOTOR VEHICLE FUEL. 

(a) Applicability and Installation Requirements 

1. Any person who owns, leases, operates or controls a motor vehicle fuel dispensing 

facility constructed or substantially modified after November 1, 1989 shall install, prior to 

commencing operation, a Stage II system as required by the terms and conditions of the 

system's currently applicable Executive. Order and any Approval Letters issued by CARB on 

or before (THE EFFECTIVE DAJE OF THE8E i\MEl'1D~ffiNT8)March I, 2009 

pursuant thereto. 

2. Any person who owns, leases, operates or controls a motor vehicle fuel dispensing 

facility constructed before November 1, 1989, that has not been substantially modified since 

November 1, 1989 shall install a Stage II system as required by the terms and conditions of 

the system's currently applicable Executive Order_and as required by the following 
Stage II Final Amendments Red line/Strikeout Copy 12-01-08 

schedule: 

a. by April 1, 1991 where the annual (calendar year) throughput of the motor 

vehicle fuel dispensing facility is greater than or equal to 1,000,000 gallons of motor 

vehicle fuel; or 

b. by April 1, 1992 where the annual (calendar year) throughput of the motor 

vehicle fuel dispensing facility is less than 1,000,000 ga,llons but greater than ot 

equal to 500,000 gallons of motor vehicle fuel; or 

c. by April 1, 1993 where the annual (calendar year) throughput of the motor 

vehicle fuel dispensing facility is less than 500,000 gallons per year but is greater 

than or equal to 20,000 gallons in any one ca1ei1.dar month; or 

d. . by April 1, 1994, or 90 days after dispensing 10,000 gallons or more in any 

calendar month, whichever is later, for all other motor vehicle fuel d~spensing 

facilities. 

3. Any person who owns, leases, operates or controls a motor vehicle fuel dispensing 

facility c()nstructed before November 1, 1989, which has not been substantially modified 

since November 1, 1989 and which has not dispensed greater than 10,000 gallons of motor 

vehicle fuel in any one calendar month since January 1, 1988 shall maintain, on site at the 

facility, monthly records of the total number of gallons of motor vehicle fuel dispensed at 

said facility for the most recent rolling five year period. · 

4. Any person who owns, leases, operates or controls a tank truck engaged in the direct 

dispensing of motor vehicle fuel to a motor vehicle or portable container shall install, by 

September 1, 1995 or prior to commencing operation, whichever is later., a Stage II system 

that meets the terms and conditions of the system's currently applicable Executive Order. 

Tank trucks dispensing motor vehicle fuel to emergency motor vehicles or portable 

containers during fire fighting activities or a declared emergency situation are exempt from 

the requirements of310 CMR 7.24(6). 

5. Any person subject to 310 CMR 7.24(6) shall conspicuously post Stage II system 

operating instructions on both sides of all motor vehicle fuel dispensers or at a position 

adjacent to the dispensers that is clec;rrly visible to the system .operator during the refueling 

process. Such instructions shall include: 

a. a clear pictorial or written description of how to correctly dispense motor 

vehicle fuel using the installed Stage II system; 

b. a warning not to continue dispensing motor vehicle fuel ("topping-off') after 

automatic system shutoff has engaged; and 

c. the telephone number of the Department's Stage IT Consumer Hotline. 

6. Stationary motor vehicle fuel storage tanks used for following purposes only shall 

be exempt from the requirements of 310 CMR 7.24(6). 

2 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

a. A stationary motor vehicle fuel storage tank of 550 gallons or less capacity, 

used for the purpose of fueling implements of husbandry, provided the fuel storage 

tank is equipped with submerged fill pipes. 

b. · A stationary motor vehicle fuel storage tank of greater than ?50 gallons. but 

1000 gallons or less capacity, used for the purpose of onsite fueling of motor 

vehicles with motor vehicle fuel that is the by-product of motor vehicle salvage yard 

operations, provided the fuel storage tank is equipped with: 

1. a submerged fill pipe; and 

u. a pressure vacuum vent valve. 

Any person who owns, leases, operates or controls a stationary motor vehicle fuel 

storage tank currently installed at a motor vehicle salvage yard and not in 

compliance with the requirements of this subsection shall take such action as 

necessary to comply with the requirements of this subsection on or before ( 1 80 days 

of the effective date of these amendments)September l. 2009. 

7. On or after (THE EFFECTIVE DATE OF THESE AMENDMENTS) March 1. 2009, any 

person who owns, leases, operates or controls a newly installed motor vehicle fuel dispensing 

facility where a Stage II system is installed in compliance with 310 CMR 7.24(6)(a) 1. shall 

install a pressure/vacuum (PN) vent cap on each underground motor vehicle fuel storage tank 

vent located at said facility, prior to commencing operation. Any person who owns, leases, 

operates or controls an existing motor vehicle fuel dispensing facility where a vapor balance 

Stage ll system is installed as of (THE EFFECTIVE DATE OF TI lESE AMENDMffi'HS)March 

1.' 2009 shall install a PN vent cap on each underground motor vehicle fuel storage tank vent on 

or before said facility's first Annual In-Use Compliance Certification submittal due date after 

(THE EFFECTIVE DATE OF THESE AMENDMENTS+ 30 days)April 1. 2009. EachPN vent 

cap shall maintain 3.0+/-0.5 inches of water pressure, and 8.0+/-2.0 inches of vacuum. Note: Per 

the applicable CARB Executive Orders. above ground motor vehi cle fuel storage tanks and all 

underground motor vehicle fuel storage tanks with vacuum assist tvpe Stage II systems are also 

required to have PN vent caps. 

(b) Operation and Maintenance Requirements 

1. Any person subject to 310 CMR 7.24(6) shall comply with the following operation 

and maintenance requirements. 

a. Operate and maintain the installed Stage II system as required by the terms 

and conditions of the system's currently applicable Executive Order. 

b. Take such actions as necessary to comply with the applicable terms and 

conditions of any new or modified Executive Order upon Department revision of 

310 CMR 7.24(6) to incorporate such new or modified Executive Order. Such 

actions shall be taken either: 

1. during applicable Routine Maintenance, Minor Modification or 

Substantial Modification of the Stage II System; or 

3 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

u. within four years, whichever occurs first. 

c. Once every seven (7) days perform a weekly visual inspection of the Stage II 

system components to determine if such components are installed, functioning and 

unbroken as required by the terms and conditions of the system's currently 

applicable Executive Order. Each visual inspection shall include, but not be limited 

to, inspection of: nozzle boots and splash/vapor guards; hoses; hose retractors, 

coaxial adaptors, dry breaks, fill caps and gaskets, vapor recovery caps and gaskets, 

spill containment boxes and drain valves. 

d. Upon determining a Stage II system component is incorrectly installed, nonfunctioning or broken during a visual inspection, immediately: 

i. repair such component(s) as required by the terms and conditions of 

the system's currently applicable· Executive Order; or 

ii. stop dispensing motor vehicle fuel through such component(s), 

conspicuously post "Out of Service" signs on such component, aud repair 

such component as required by the terms and conditions of the system's 

currently applicable Executive Order within 14 days of the date such 

component is determined to be incorrectly installed, non-functioning or 

broken. 

e. if an incorrectly installed, non-functioning or broken component cannot be 

repaired as required by 310 CMR 7.24(6)(b) l.d., such component shall inimediately 

be Isolated. "Out of Service" signs shall be conspicuously posted on said Isolated 

components until such time as said component areis correctly repaired as required 

by the Stage II system's currently applicable Executive Order. 

f. If an incorrectly installed, non-functioning or broken component cannot be 

repaired or tsetatelsolated as required by 310 CMR 7 .24( 6)(b )_ l.d. or e., the facility 

owner/operator shall immediately stop dispensing motor vehicle fuel and 

conspicuously post "Out of Service" signs on all motor vehicle fuel dispensers until 

such time as all incorrectly installed, non-functioning or broken components are 

correctly repaired as required by the terms and conditions of the Stage II system's 

currently applicable Executive Order. 

2. A visual inspection of a Stage II system to meet the requirements of 310 CMR 

7.24(6)(b)l.c. shall be performed only by a person who is trained to operate and maintain 

the Stage II system as required by the terms and conditions of the system's currently 

applicable Executive Order. A current record of all persons trained shall be maintained on 

site or, for tank trucks, at the address from which the tank truck is principally operated, 

and shall include the following: 

a. the date training was last received; 

b. the trainee's printed name; and 

c. the personal signature of the trainee acknowledging receipt of the training. 

4 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

3. Any person subject to 310 CMR 7.24(6) shall maintain all Stage II system 

maintenance records on site, in a centralized location, for the most recent rolling twelvemonth period. Such records may be either (a) hard copy documents or (b) electronic 

documents, provided that a hard copy of the electronic documents shall be printed on-site 

immediately upon reque~t. Such maintenance records for tank trucks shall be maintained at 

the .address from which the tank truck is principally operated. Stage II system maintenance 

records shall include: 

a. all of the facility's weekly inspection checklists for the prior rolling twelvemonth period, identifying: 

i. the date each weekly visual inspection was performed and the 

signature of the person who performed the visual inspection; 

ii. any Stage II system componeht determined to be incorrectly 

installed, non-functioning or broken; 

m. whether the identified incorrectly installed, non-functioning or 

broken component was immediately repaired, taken out of service and 

repaired within 14 days, Isolated, or the facility stopped dispensing motor 

vehicle fuel and all fuel dispensers were taken out of service; 

iv. the date the incorrectly installed, non-functioning or broken 

component.B_ identified in iii. above :waswere repaired. 

b. A copy of compliance testing company test results for all Stage II 

compliance tests during the prior rolling twelve-month period. 

c. A copy of the Stage II system's most recent Annual In-Use Compliance 

Certification. 

4. All records maintained pursuant to 310 CMR 7.24(6)(b) 2. and 3. shall be made 

available to the Department or the US EPA immediately upon request. In the event 

requested records cannot be made immediately available, requested records shall be 

delivered to the Department or the US EPA, as applicable, within 24 hours of the initial 

request. 

(c) Compliance Testing and Certification Requirements 

1. Stage ll system testing, record keeping and certification as a result of Routine 

Maintenance or Minor Modification of a Stage II system. 

a. In the event of Routine Maintenance, a record of such maintenance shall 

be maintained in accordance with 310 CMR 7.24(6)(b) 3. Compliance testing and 

submittal of a compliance c-ertification to the Department is not required. 

b. In the event of a Minor Modification of a Stage II system, applicable 

compliance tests shall be performed and passed prior to commencing system 

operation and a record of such modification and test results shall be maintained in 

5 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

accordance with 310 CMR 7.24(6)(b) 3. Submittal of a compliance certification to 

the Department is not required. 

2. Installation/Substantial Modification Certification. Any person subject to 310 CMR 

7.24(6) who installs or makes a Substantial Modification to a Stage II system after ~ 

~G+WE-DATE OF---THE.£E...-ABN~-)March L 2009, shall, .prior to 

commencing operation, perform and pass all applicable compliance tests pursuant to 310 

CMR 7.24(6)(d). and submit to the Department within 7 days of performing and passing 

said tests, a fully completed and signed Installation/Substantial Modification Cettification, 

on a form obtained from the Department, attesting to the following: 

a. the installed or substantially modified Stage II system ts installed or 

substantially modified in compliance with 310 CMR 7 .24( 6)( a); 

b. all applicable compliance tests as required by 310 CMR 7 .24( 6)( d) were 

performed and passed; and 

c. the applicable installation compliance tests were performed and passed not 

more than 30 days ptior to the date postmarked on the envelope used to submit the 

Certification to the Depattment. · 

3. Annual In-Use Compliance Certification. Except as provided in 310 CMR 

7.24(6)(c) L any person subject to 310 CMR 7.24(6) shall annually submit to the 

Department a fully completed and signed Annual In-Use Compliance Certification, on a 

form obtained from the Department, attesting to the following: 

a. the installed Stage II system is operated and maintained as required by 310 

CMR 7.24(6)(b); 

b. the following in-use compliance tests, as applicable, were .Performed as 

required by 310 CMR 7.24(6)(d): 

i. Vapor balance systems. 

Annual in-use compliance test~: Pressure Decay Test; Vapor-Tie Test; PN 

Vent Test. 

Every-third-year in-use compliance test: Dynamic Pressure/Liquid Blockage 

Test. · 

ii. Vacuum assist systems. 

Annual in-use compliance tests: Pressure Decay Test; Vapor-Tie Test; PN 

Vent Test; and Air-to-Liquid Ratio Test. 

Every-third-year in-use compliance test: Dynamic Pressure/Liquid Blockage 

Test. 

111. Healy systems. 

All applicable tests shall be performed annually. 

c. The applicable in-use compliance tests were performed and were-passed not 

6 
Stage II Final Amendments Redline/Strikeout Copy.12-01-08 

more than 30 days prior to the date postmarked on the envelope used to submit the 

Certification to the Department. 

4. Alternative Annual In-Use Compliance Certification. Any person subject to 310 

CMR 7.24(6) who submits two consecutive years of Annual In-Use Compliance 

Certifications ~HFSttafl:He in compliance with 310 CMR 7.24(6)(c) 3. in which all applicable 

in-use compliance tests were passed on the first try, as certified te as require4-9y-pursuant to 

310 CMR 7.24(6)(g)8., may elect to submit annually to the Department an Alternative 

Annual In-Use Compliance Certification on a form obtained from the Department: 

a. Facilities meeting the requirements of310 CMR 7.24(6)(c) 4. and electing to 

submit an Alternative Annual In-Use Compliance Certification shall be: 

i. exempt from annual Stage II compliance testing requirements in the 

year following the submittal of two consecutive years' of Annual In-Use 

Compliance Certifications in compliance with 310 CMR 7.24(6)(c) 4.; and 

ii. subject to all applicable Stage II compliance tests as referenced in 

310 CMR 7.24(6)(d) in the second year following the submittal of two 

consecutive years' Annual In-Use Compliance Certifications in compliance 

with 310 CMR 7.24(6)(c) 3., and every other year thereafter. 

b. Any person submitting an Alternative Annual In-Use Compliance 

Certification to the Department shall fully complete and sign said Certification and 

attest to the following: 

i. the installed Stage II system is correctly operated and maintained as 

required by 31 0 CMR 7 .24( 6)(b); 

ii. all applicable compliance tests were performed and passed as 

required by 310 CMR 7.24(6)(c) 4.a.ii., and 

111. The applicable compliance tests were performed and were passed 

not more than 30 days prior to the date postmarked on the envelope used to 

submit the Certification to the Department. 

c. Any person submitting an Alternative Annual In-Use Compliance 

Certification and fails one or more compliance certification tests on the first try as 

required by 310 CMR 7.24(6)(c) 4. shall be required, in subsequent years, to 

annually certify in compliance with the requirements of 310 CMR 7.24(6)(c) 3., 

until su ch time as #iesaid person meets the requirements in 31 0 CMR 7 .24( 6)( c) 

4. 

5. Annual In-Use Compliance Certification Submittal Requirements. The annual 

submittal date for Certifications required pursuant to 310 CMR 7.24(6)(c) 3. and 4., is no 

later than: 

a. For persons subject to 310 CMR 7.24(6) who install or make a Substantial 

Modification to a Stage II system on or after January 1, 2001, the anniversary of the 

7 
Stage II Final Amendments Redline/Strikeout Copy 12-01 -08 

date postmarked on the envelope used to submit to the Department the Installation 

Compliance Certification required by 310 CMR 7 .24( 6)( c) 1. or the date the facility 

commenced operation, whichever occurs first; and 

b. For all other persons subject to 310 CMR 7.24(6), May 1, 2002, or a date 

otherwise provided by the Department, whichever is earlier. Persons subject to 310 

CMR 7.24(6)(c) 5.b. who are provided an annual submittal date by the Department 

shall be notified by the Department of their first annual submittal date and· required 

in-use compliance tests pursuant to 310 CMR 7.24(6)(c) 3.b. no less than 90 days 

prior to the first annual submittal date established by the Department. 

c. Upon request of any person subject to 310 CMR 7.24(6), the Department 

may revise said person's annual Certification submittal date. Such revision shall set 

a revised annual submittal date that is no more than 12 months after the otherwise 

applicable submjttal date. 

6. Any person who owns, leases, operates or controls a Stage II system that fails one or 

more in-use compliance tests required by 310 CMR 7.24(6)-t@ 3.:. or 4., shall immediately: 

a. repair incorrectly installed, non-functioning or broken component as 

required by the terms and conditions of the Stage II system's currently applicable 

Executive Order; 

b. re-test and pass each failed test; and 

c. submit to the Department the required Annual In-Use Compliance 

Certification on or before the facility's Annual In-Use Compliance Certification 

submittal date or within 30 days of the date of the Stage II system~s first passing test 

result as required by 310 CMR 7.24(6)(c) 3.c. or 310 CMR 7.24(6)(c) 4.c., as 

applicable, whichever occurs first. 

7. If a facility fails one or more required in-use compliance tests and the incorrectly 

installed, non-functioning or broken components cannot be repaired as required by 310 

CMR 7.24(6)(c) 7., the facility owner/operator shall. immediately: 

a. i-se-1-a:teisolate the incorrectly installed, non-functioning or broken 

components from the Stage II system so that the remainder of the Stage ll system 

operates as required by the terms and conditions of the system's currently applicable 

Executive Order; and 

b. submit to the Department the required Annual In-Use Compliance 

Certification based on passing test results for the remainder of the Stage II system on 

or before the facility's Annual In-Use Compliance Certification submittal date or 

within 30 days of the date of the Stage II system's first passing test result as required 

by 310 CMR 7.24(6)(c) 3.c. or 310 CMR 7.24(6)(c) 4.c., as applicable, which ever 

occurs first. 

c. Any Stage II system component Isolated from the remainder of the Stage ll 

System shall remain Isolated i.mtil such time as: 

8 
· I Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

i. said component is repaired as required by the terms and conditions 

of the Stage II System's currently applicable Executive Order; and 

ii. all applicable, compliance testing, record keeping and certification 

requirements for the Routine Maintenance, Minor Modification, or 

Substantial Modification of a Stage II system are complied with. 

8. If a facility fails one or more required in-use compliance tests and the incorrectly 

installed, non-functioning or broken Stage II system component cannot be repaired as 

required by 310 CMR 7 .24(6)( c) 6. or 7 ., the facility owner/operator shall immediately stop 

dispensing motor vehicle fuel and conspicuously post "Out of Service" signs on all motor 

vehicle fuel dispensers until such time as: 

a. all incorrectly installed, non-functioning or broken components are repaired 

as required by the terms and conditions of the Stage II system's currently applicable 

Executive Order; 

b. all applicable in-use compliance tests are performed and passed as required 

by 310 CMR 7.24(6)(c) 3. or 4., as applicable; and 

c. a fully completed Annual In-Use Compliance Certification has been 

submitted to the Department as required by 310 CMR 7 .24( 6)( c) 3. 

d. If a facility fails one or more required in-use compliance tests and is subject 

to 310 CMR 7.24(6)(c) 8., for purposes of compliance with the Annual In-Use 

Compliance Certification submittal requirements of 31 0 CMR 7 .24( 6)( c) 3. or 4., 

said facility owner/operator shall submit to the Department a fully completed and 

signed Stage II System Closure Notification as required by 310 CMR 7 .24( 6)( e) 2. 

on or before said facility's currently applicable Annual In-Use Compliance 

Certification submittal due date. 

9. Any Certification submitted to the Department as required by 31 0 CMR 7 .24( 6)( c) 

shall be signed by a Stage II System Responsible Official as required by 310 CMR 

7.24(6)(£). 

10. Any person subject to 310 CMR 7.24(6), upon written notice from the Department, 

shall perform such compliance tests as the Department determines necessary to demonstrate 

the Stage II system is installed and maintained as required by the terms and conditions of 

the system's currently applicable Executive Order and shall submit the results to the 

Department within 14 days of the performance of said tests. 

(d) Stage II System Compliance Testing Requirements 

For the purposes of 310 CMR 7 .24( 6)( c), the following Stage II System compliance tests 

and requirements shall be required: 

1 . Vapor Balance systems. 

Pressure Decay Test, Vapor-Tie Test, PN Vent Test and Dynamic Pressure/Liquid 

Blockage Test 

9 
Stage II Final Amendments Redline/Strikeout Copy 12-01 -08 

2. Vacuwn Assist systems. 

Pressure Decay Test, Vapor-Tie Test, PN Vent Test, Air-to-Liquid Ratio Test and 

Dynamic Pressure/ Liquid Blockage Test 

3. Healy systems. 

a. Healy 400 ORVR (Executive Order # G-70-186), Healy 400 ORVR 

Above Ground Storage System (Executive Order # G-70-187) and Franzen-Hill 

Cargo Tank Truck System (Executive Order # G-70-193): 

Pressure Decay Test: 

Vapor Tie Test; 

PN Vent Test; 

Exhibit 4: Vapor Return Line Vacuum Integrity Test; and 

Exhibit 5: Fillneck Vapor Pressure Regulation Fueling Test. 

b. Healy 600 (Executive Order # G-70-165): 

Pressure Decay Test; 

Vapor Tie Test; 

PN Vent Test; 

Air-to-Liquid Ratio Test; and 

Exhibit 4: Vapor Return Line Vacuum Integrity Test. 

4. Compliance tests performed to meet the requirements of 310 CMR 7.24(6)(c) shall 

be performed only by a person or Stage ll compliance testing company. that has 

submitted to the Department a Stage II Compliance Testing Company Notification 

as required by 31 0 CMR 7 .24( 6)(g) 1. 

(e) Notification Requirements. 

1. Any person, upon entering into a purchase, lease or other contractual agreement by 

which said person becomes the owner, operator, lessee or controller of an existing motor 

vehicle fuel dispensing facility or tank truck subject to 310 CMR 7.24(6) shall submit to the 

Department, within 30 days of the effective date of becoming such an owner, operator, 

lessee or controller or within 10 days of a written request from the Department, a fully 

completed New Stage ll System Owner, Operator, Lessee or Controller Notification on a 

form obtained from the Department. 

a. +ReSaid Notification shall include the following: 

i. the name of the new Stage II system owner, operator, lessee or 

controller and related business documentation, including the name and 

address of the facility where the Stage ll system i.s located or from which the 

tank truck is principally operated; and 

11. the effective date said person became the new owner, operator, 

lessee or controller. 

b. A&ySaid Notification shall be signed by the individual who is a Responsible 

Official for the new owner, operator, lessee or controller regarding the Stage II 

10 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

system, who shall attest to the following: 

i. I certify that I personally examined the foregoing and am familiar 

with the information contained in this document and all the attachments and 

that, based on my inquiry of those persons inunediately responsible for 

obtaining the information, I believe that the information is true, accurate and 

complete. I am aware that there are significant penalties for submitting false 

information, including possible fmes and imprisorunent; 

ii. I am fully authorized to make this attestation on behalf of this facility 

or tank truck, as applicable. 

2. Any person subject to 31 0 CMR 7 .24( 6), upon entering into a sale, lease or other 

contractual agreement by which said person relinquishes his .or her authority as an owner, 

operator, lessee or controller of a facility or tank truck subject to 310 CMR 7.24(6), shall 

submit to the Department, within 30 days of the effective date of said sale, lease or other 

contractual agreement, a signed letter notifying the Department of the following: 

a. the name of the. person relinquishing his or her authority as an owner, 

operator, lessee or controller of the facility or tank truck subject to 310 CMR 

7.24(6), the facility name, Stage II Facility Customer Code NwnberDEP Facilitv 

Account Ntm1ber and address or the address from which the tank truck is principally 

operated, as applicable; 

b. the name of the new owner, operator, lessee or controller of the facility or 

tank truck subject to 310 CMR 7.24(6) and related business information, including 

the new facility name and address or the address from which the tank truck is 

principally operated, as applicable; and 

c. the effective date of the change of owner, operator, lessee or controller. 

3. Any person subject to the requirements of 31 0 CMR 7 .24( 6) seeking to permanently 

or temporarily take out of use an existing motor vehicle fuel dispensing facility or tank truck 

shall submit to the Department a fully completed and signed Stage ll System Closure 

Notification, on a form obtained from the Department. 

a. Said Notification shall include the following: 

i. the name of the Stage II facility owner, operator, lessee or controller 

and related business information, including the name and address of the 

facility where the Stage II system was located or from which the tank truck 

was principally operated, as applicable; 

ii. the Stage-H-f"Ueil#:y-GI:Jsteme:F-teae-fl.tlflffieFDEP Facility Account 

Number for the applicable facility or tank truck; and 

111. a fully completed Netifieatietr-For Storage TanJcs Reg~E~' 

527 CMR 9.00 (FP 290) Foffil, as ss ~eal-Fi;:e--f}e~aftfl-1~1ft, 

11 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

OO€Bfflentffig that the ap~le-fue-i -tfl:l€k--is ei:ther permanently 

e-t~-ake-H:-&l:lt-ef-1:15e:-a copy of the Notification For Removal or 

Closure of In Place Underground Storage Tanks Regulated Under 527 

CMR 9.00 CFP-290R) Form, documenting the permanent or tempormy out 

of use status of said facility or tank truck on record with the 

Massachusetts Department of Fire Safety. 

b. The temporary out of use status of a motor vehicle fuel dispensing system 

shall be renewed as necessary by any person subject to the requirements of 31 0 

CMR 7.24(6) by submitting a new, fhllv completed Stage II System Closure 

Notification, on or before the annual · anniversaty of the effective date said 

dispensing system was taken out of use, as noted in the required. FP-290R Form. 

Said renewal shall include a cmrent FP-290R Form for said dispensing system on 

record with the Massachusetts Department of Fire Safety documenting the 

·system's continued temporary out of use status. Aa:y:--'f:~erson subject to tHe 

R-"'Eftti-fe.m:€ftts of 310 CMR 7.21(6) ·.vho temporarily takes out of use a Ft.letet: 

vehicle fuel dispensing facil ty-s-lT&l~r-tB-re commencing the distribution of 

motor vehicle fuet,perffiFm-aad-pass-aH-applicable compliance tests and submit-to 

the Dep~llly coffil*eted Installation/Substantial Moffifi:eatiBn 

Gerfi.fieattan-afl-fe£ttt.ire<4 by 310 CMR 24(61fcj-h-~em~ 

sl.:ia.J.~ be reRe-~ec~g-aR-~fully completed 

Installation/Substantial Med-i.fi:e.atien-Cer#.fi:catie&,---efl---Of'-befure the annual 

anniversary ~he date the local Fire Department signed the requir-ed FP 290 F01m . 

~enev•al-sltttl-l--i:nelOO.e-a--&Ufren-t--FP~rm, as issued by the local Fife 

Depaflffient, docum:en:tiflt:,'-the-fac.i:l:iifs-c-emimred-temp<:tffiry out of use st~ 

c. Anv person subject to the requirements of 310 CMR 7.24(6) who 

temporarily takes out of use a motor vehicle fuel dispensing system shall. prior to 

commencing the distribution of motor vehicle fuel. perform and pass all 

.@.plicable compliance tests a11d submit to the Department a fully completed 

Installation/Substantial Modification Ce1tification as required by 3l0 CMR 

7 .?4( 6 )(c) 2. 

cQ.. Any person subject to the requirements of 310 CMR 7.24(6), where the 

motor vehicle fuel dispensing facility is e#lier-permanently or temporarily taken out 

of use, shall no longer be subject to 310 CMR 7 .24( 6) as of the effective date the 

facility was pe1manently taken out of serviceuse as referenced in the required FP290B, Form. 

4. Any Notification submitted to the Department as required by 310 CMR 7.24(6)(e) 

shall be signed by a Stage II System Responsible Official as required by 310 CMR 

7.24(6)(f). 

(f) Stage II System Responsible Official Certification of Compliance. 

1. Except in circumstances described in 310 CMR 7.24(6)(f) 2., any Certification or 

Notification required by 310 CMR 7.24(6)(c) or (e) shall be signed by an individual who 

is ·a Responsible Official regarding Stage II system compliance. 

12 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

2. For Stage II systems owned by one party and leased, operated or controlled by 

another independent party and where both parties have separate Stage II compliance 

responsibilities, any Certification or Notification submitted in compliance with the 

requirements of 310 CMR 7.24(6)(c) or (e) shall be signed by Responsible Officials for 

each party regarding Stage II system compliance. Each Stage II System Responsible 

Official shall attest to the following: 

i. I certify that I personally examined the foregoing and am familiar with the 

information contained in this document and all the attaclunents and that, based on 

my inquiry of those persons immediately responsible for obtaining the information, I 

believe that the information is true, accurate and complete. I am aware that there are 

significant penalties for submitting false information, including possible fines and 

imprisonment; 

ii. ~hat systems to maintain compliance are in place at the facility or, if 

applicable, at the location from which the tank truck is principally operated and will 

be maintained for the coming year even if the processes or operating procedures are 

changed over the course of the year; and 

111. I am fully authorized to make this attestation on behalf of this facility or tank 

truck, as applicable. 

3. Any person immediately responsible for obtaining information referenced in 31 0 

CMR 7.24(6)(±), who knowingly and willfully makes false, inaccurate, incomplete or 

misleading statements pursuant to any Certification or Notification required under 310 

CMR 7 .24( 6), may be in violation of 31 0 CMR 7 .24( 6). Not withstanding the previous 

sentence, any person subject to the requirements of 310 CMR 7.24(6), shall comply with all 

applicable provisions of 310 CMR 7 .24( 6). 

Compliance Testing Company Requirements 

L On or after fR.J.E EFFECH¥E-M+E-GF-+I4ESE-AMENDMEN~Mru:ch 1, 

2009, any person who owns, leases, operates or controls a company that performs Stage II 

compliance tests to meet the requirements of 310 CMR 7 .24( 6)( c) shall submit to the 

Department a fully completed Stage II Compliance Testing Company Notification, on a 

form obtained from the Department, prior to performing any required Stage II compliance 

test. 

a. the Notification shall include the following: 

i. the name and business mailing address of the Stage II compliance 

testing company owner, operator, lessee or controller; 

ii: the name and address of any business that is engaged in the 

installation or Substantial Modification of Stage II systems and is owned, 

operated, leased or controlled by, or affiliated with the owner, operator, 

lessee or controller of the compliance testing company; 

m. the name and address of any motor vehicle fuel dispensing facility or 

tank truck subject to 310 CMR 7.24(6) that is owned, operated, leased or 

13 
Stage II Final Amendments Red line/Strikeout Copy 12-01-08 

controlled by, or affiliated with the owner, operator, lessee or controller of 

the compliance testing company; 

1v. the address and telephone number of the facility(ies) from which the 

daily compliance testing activities of the compliance testing company 

originate and at which any records required by 31 0 CMR 7 .24( 6)(g) 10. are 

maintained; 

v. a written description of the employee training systems in place at the 

compliance testing company to ensure required compliance tests are 

performed as required ·by applicable protocols and procedures, pursuant to 

310 CMR 7.24(6)(g)6. and 7; and 

vi. a list of all Compliance Testing Company Responsible Officials with 

the authority to sign Compliance Testing Company Certifications on behalf 

of the compliance testing company. 

b. Each Notification shall be signed by an individual who is a Responsible 

Official regarding the compliance testing company, .who shall attest to the 

following: 

i. I certify that I personally examined the foregoing and am familiar 

with the information contained in this document and all the attachments and 

that, based on my inquiry of those persons immediately responsible for 

obtaining the information, I believe that the information is true, accurate and 

complete. I am aware that there are significant penalties for submitting false 

information, including possible fines and imprisonment; 

11. Employee training systems are in place at the company to ensure 

Stage IT compliance tests are performed as required by all applicable 

protocols and procedures and such training systems will be maintained for 

the coming year ev~n if the protocols and procedures are changed over the 

course of the year; and 

111. I am fully authorized to make this attestation on behalf of this Stage 

IT Compliance Testing sCompany. 

2. Any person subject to the requirements of 310 CMR 7.24(6)(g) shall notify the 

Department in writing of any change to the information submitted to the Department 

pursuant to· 310 CMR 7 .24( 6)(g) 1. within 14 days of the effective date of such change. 

Upon the Department's written request, the person shall submit a fully revised and 

completed Notification to the Department as required by the requirements of 310 CMR 

7 .24( 6)(g) 1. 

3. No person subject to 310 CMR 7.24(6)(g) shall perform any Stage IT compliance 

test unless said person has first been trained in accordance with the applicable compliance 

test protocols and procedures required by 310 CMR 7.24(6)(g) 6. and 7. 

4. Any person subject to the requirements of 310 CMR 7.24(6)(g) shall submit, at least 

14 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

once every two weeks, a written list to the Department identifying all motor vehicle fuel 

dispensing facilities and tank trucks at which the company is scheduled to perform required 

Stage II compliance test(s) over the next 14 day period. 

a. The list shall be organized by Department region and date, and shall include 

the name and address of each facility or tank truck to be tested, the applicable 

section under 310 CMR 7.24(6)(c) -l-2_., 2-J., or ;4., the required compliance tests 

sha±lto be performed, and the estimated time that the company expects to arrive at 

the facility location. 

b. The Department shall be notified, in writing, of any change of date of an 

individual facility's scheduled compliance tests no later than 9a.m. of the day the 

scheduled test(s) is to occur. Additions to a submitted compliance-testing schedule 

shall be submitted to the Department, in writing, no less than two working days 

prior to the date of any scheduled test. 

c. Failure to comply with the Notification requirements of310 CMR 7.24(6)(g) 

4. may be a basis for the Department to determine that tests conducted after 

inadequate notice are invalid. 

5 Any person subject to the requirements of 310 CMR 7.24(6)(g) shall immediately 

notify the Department of any failed Stage II compliance tests performed as required by 31 0 

CMR 7 .24( 6)( c) if said person did not return to retest the Stage II system as required by 3 1 0 

CMR 7.24(6)(c) 6. or 7. on or before the facility's Annual In-Use Compliance Certification 

submittal date, or within 30 days of the date of the Stage II system's first passing test result, 

which ever occurs first. Said person shall notify the Department regarding the name and 

address of the facility, and the facility's Facility Account Number. 

6. Any person subject to 310 CMR 7.24(6)(g) shall perform compliance tests to meet 

the requirements of310 CMR 7.24(6)(c) only upon confirmation that: 

a. all above ground Stage II system components including, but not limited to: 

dispensers~ nozz es~ swivels~ hose retractors; hoses; breakaways~ vapor check 

valves; and the pressure/vacuum valve(s) are installed as required and are the correct 

components as required by the terms and conditions of the system's currently 

applicable Executive Order; and 

b. all motor vehicle fuel dispensing facilities with two or more motor vehicle 

fuel storage tanks are properly manifolded as required by the terms and conditions 

of the system's currently applicable Executive Order. 

7. Any person subj ect to 310 CMR 7.24(6)(g), shall perform Stage II compliance tests 

to meet the requirements of 310 CMR 7.24(6) only in accordance with the applicable 

CalifOrnia Air Resources Board test procedures cited qelow: 

a. Pressure Decay Test (Bay Area Air Pollution Control District Source Test 

Procedure ST-30 (2/6/1991)) and Table A. Minimum Allowable Pressure. 

I Table A. MINIMUM ALLOWABLE PRESSURE (Based on an initial pressure of 1 0.0" we.) 

15 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

Ullage Minimum Allowable Ullage Minimum Allowable 

(Gal) Pressure ("we) (Gal) · Pressure ("we) 

500 3.70 6,000 9.38 

600 4.50 7 000 9.46 

700 5.20 7,500 9.50 

800 5.80 8 000 9.52 

900 6.20 9,000 9.56 

1,000 6.50 10,000 9.60 

1,250 7.05 11,000 9.62 

1,750 7.90 12,000 9.64 

2,000 8.20 13,000 9.66 

2,250 8.35 14,000 9.68 

2,500 8.50 15,000 9.70 

2,750 . 8.60 16,000 9.71 

3,000 8.70 17,000 9.71 

3,250 8.80 18,000 9.72 

3,500 8.90 19,000 9.73 

3,750 9.00 20,000 9.73 

4,000 9.10 21,000 9.74 

4,250 9.15 22,000 9.75 

4,500 9.20 23,000 9.75 

4,750 9.25 24,000 9.76 

5,000 9.30 25,000 9.77 

30,000 9.80 

Note: For a valid test, total ullage must be at e~t 500 gallons but no more than 30,000 gallons. 

b. Underground Piping Check (Vapor Tie) Test (San Diego County Air 

Pollution Control District Test Procedure TP-96-1, Section 5.1.9) 

c. PressureNacuum Vent Test (Leak Rate and Cracking Pressure of 

PressureNacuum Vent Valves, CARB TP-201.1E) PN reliefvents shall be tested 

to be within .29oz/in2 or 0.5 inches of water column of the designed pressure and 

within 1.2oz/in2 or 2.0 inches of water column of the vacuum settings. 

d. Air-to-Liquid Volume Ratio Test (CARB TP-201.5). 

e. Dynamic Pressure/Liquid Blockage Test (CARB TP-201.4). 

f. Healy 400 ORVR (Executive Order # G-70-186), Healy 400 ORVR 

Above Ground Storage System (Executive Order # G-70-187) and Franzen-Hill 

Cargo Tank Truck System (Executive Order # G-70-193) 

Exhibit 4: Vapor Return Line Vacuum Integrity Test 

Exhibit 5: Fillneck Vapor Pressure Regulation Fueling Test 

Healy 600 (Executive Order # G-70-165) 

Exhibit 4: Vapor Return Line Vacuum Integrity Test. 

8. Any person subject to 310 CMR 7.24(6)(g) shall certify to the Department that each 

16 
Stag·e II Final Amendments Redline/Strikeout Copy 12-01-08 

compliance test performed to meet the requirements of 310 CMR 7 .24( 6)( c) was performed 

as required by 310 CMR 7.24(6)(g) 6. and 7. ~+ifeeAs applicable. the Certification 

shall be submitted on the applieahleg Stage II Installation/Substantial Modification 

Certification or Annual In-Use Compliance Certification_. as applicable. The requir~d 

Certificationand· shall include: 

a. the date each compliance test was frrst performed and the result; and 

b. the date each compliance test was performed and passed. 

c. a notation whether, (i) the entire installed Stage II system was tested and 

passed all applicable compliance tested or (ii) incorrectly installed, non-functioning 

or broken components were Isolated from the remainder of the installed Stage n 

system and the remainder· of Stage II system was tested and passed all applicable 

compliance tests. 

d. If the remainder of the Stage II system was tested and passed all applicable 

compliance tests, as noted in 310 CMR 7 .24( 6)(g) 8.c., identify all components 

Isolated from the remainder of the Stage II system. 

9. Each Certification submitted pursuant to 310 CMR 7.24(6)(g) 8. shall be fully 

completed and signed by a Compliance Testing Company Responsible Official, who shall 

attest to the following: 

a. I certify that I personally examined the foregoing and am familiar with the 

information contained in this document and all the attachments and that, based on 

my inquiry of those persons immediately responsible for obtaining the information, I 

believe that the information is true, accurate and complete. I am aware that there are 

significant penalties for submitting false information, including possible fines and 

imprisonment; and 

b. I am fully authorized to make this attestation on behalf of this Stage II 

Compliance Testing cCompany. 

10. · Any person subject to 310 CMR 7.24(6)(g) shall maintain the following records on 

site~ for a minimum of five years, at the location(s) referenced on the form submitted 

pursuantto310CMR 7.24(6)(g) l.a.iv: 

a. A complete set of records of compliance tests performed to meet the 

requirements of310 CMR 7.24(6)(c). Such records shall include, by facility address: 

1. the date and first result for each required test performed; 

n. the date each test was performed and passed; and 

111. an itemized list of all Stage II system components re-installed, 

repaired or replaced as necessary for the system to pass the applicable test(s). 

17 
Stage II Final Amendments Redline/Strikeout Copy 12-01 -08 

b. A current record of all persons or employees trained as required by 310 

CMR 7.24(6)(g)3. Such record shall inch.~de the following: i. the date training was 

received; ii. the person or employee's printed name; and iii. the personal signature of 

the person or employee acknowledging receipt of required training. 

11. All records maintained pursuant to 310 CMR 7.24(6)(g) 10. shall be made available 

to the Department or the US EPA inunediately upon the request of either. 

(h) Violations of310 CMR 7.24(6) 

For any person subject to 310 CMR 7.24(6) it shall be a violation of310 CMR 7.24(6) to: 

1. fail to submit any Certification or Notification required by to 310 CMR 7 .24( 6) as 

applicable; 

2. make any false, inaccurate, incomplete or misleading $tatements in any Certification 

or Notification required by to 310 CMR 7 .24(6); 

3. make any false, inaccurate, incomplete or misleading statements in any record, 

report, plan, file, log or register which said person is required to keep pursuant to 310 CMR 

7.24(6); 

4. hold themselves out as a responsible official in violation of the applicable · 

requirements ofto 310 CMR 7.24(6); 

5. fail to comply with any applicable standards imposed under 310 CMR 7.24(6); or 

6. violate any other provision of 310 CMR 7 .24( 6). 

(i) Department Adopted CARB Stage II System Executive Orders. 

Number Description 

G-70-7-AD Certification of the Hasstech Model VCP-2 and VCP 2A Phase II Vapor 

Recovery System. 

G-70-14-AA Recertification of Red Jacket Aspirator Assist Phase II Vapor Recovery 

System. 

G-70-17-AD Modification of Certification of the Emco Wheaton Balarice Phase II Vapor 

Recovery System. 

G-70-18-C Modification of Certification of the Shell Model 75B1 and 75B1-R3 Service 

Station Phase II Vapor Recovery System. 

G-70-23-AC Recertification of the Exxon Balance Phase II Vapor Recovery.System. 

G-70-25-AA Recertification of the Atlantic Richfield Balance Phase II Vapor Recovery 

System. 

G-70-33-AB Certification of the Modified Hirt VCS-200 Vacuum Assist Phase IT Vapor 

Recovery System. 

G-70-36-AD Modification of Certification of the OPW Balance Phase TI Vapor Recovery 

System. 

G-70-37-B Modification of the Certification of the Chevron Balance Phase II Vapor 

Recovery System with OPW nozzles for Service. 

18 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

G-70-38-AB Recertification of the Texaco Balance Phase II Vapor Recovery System. 

G-70-48-AA Recertification of the Mobil Oil Balance Phase II Vapor Recovery System. 

G-70-49-AA Recertification of the Union Balance Phase II Vapor Recovery System. 

G-70-52·AM Certification of Components for Red Jacket, Hirt and Balance Phase II Vapor 

Recovery System. 

G-70-53-AA Recertification of the Chevron Balance Phase ll Vapor Recovery System. 

G-70-77 Certification of the OPW Repair/Replacement Parts and Modification of the 

Certification of the Ol>W Balance Phase II Vapor Recovery System. 

G-70-78 Certification of the E-Z Flo Nozzle Company Rebuilt Vapor Recovery Nozzles 

and Vapor Recovery Components. 

G-70-101-B Certification of the E-Z Flo Model 3006 and 3007 Vapor Recovery Nozzles 

and Use of E-Z Flo Components with OPW Models. 11 VC and 11 VE Vapor 

Recovery Nozzles. 

G-70-107 Certification of Rainbow Petroleum Products Model RA3003, RA3005, 

RA3006 and RA3007 Vapor Recovery Nozzles and Vapor Recovery 

Components. 

G-70-110 Certification of Stage I and ll Vapor Recovery Systems for Methanol Fueling 

Facilities. 

G-70-118-AB Certification of Amoco V -1 Vapor Recovery System. 

G-70-125-AA Modification of the Certification of the Husky Model V Phase II Balance Vapor 

Recovery Nozzle. 

G-70-127 Certification of the OPW Model 111-V Phase Vapor Recovery Nozzle. 

G-70-134 Certification of the EZ Flo Rebuilt A-4000 Series and llV-Series Vapor 

Recovery System. 

G-70-139 Addition to the Certification of the Hirt Model VCS-200 Phase II Vapor 

Recovery System. 

G-70-150-AE Modification of the Certification of the Gilbarco VaporVac Phase ll Vapor 

Recovery System. 

G-70-153-AD Modification to the Certification of the Dresser/Wayne WayneVac Phase ll 

Vapor Recovery System. 

G-70-154-AA Modification to the Certification of the Tokheim MaxVac Phase II Vapor 

Recovery System. 

G-70-159-AB Modifiaction of the Certification of the Saber Nozzle for Use with the Gilbarco 

VaporVac Phase ll Vapor Recovery System. 

G-70-163-AA Certification of the OPW VaporEZ Phase II Vapor Recovery System. 

G-70-164-AA Modification to the Certification of the Hasstech VCP-3A Vacuum Assist 

Phase II Vapor Recovery System. 

G-70-165 Healy Vacuum Assist Phase II Vapor Recovery System. 

G-70-169-AA Modification to the Certification of the Franklin Electric INTELLIV AC Phase 

ll Vapor Recovery System. 

G-70-170 Certification of the EZ-flo Rebuilt 5005 and 5015 for use with the Balance 

Phase II Vapor Recovery System. 

G-70-177-AA Certification of the VCS400-7 Vacuum Assist Phase II Vapor Recovery 

System. 

G-70-179 Certification of the Catlow ICVN-V1 Vacuum Assist Phase II Vapor Recovery 

System. 

19 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

G-70-180 Order Revoking Certification of the Healy Phase IT Vapor Recovery Systems 

for Gasoline Dispensing Systems. 

G-70-183-AA Certification of the Healy/Franklin Vacuum Assist Phase IT Vapor Recovery 

System. 

G-70-186 Certification of the Healy Model400 ORVR Vapor Recovery System. 

G-70-188 Certification of the Catlow ICVN Vapor Recovery Nozzle System for use with 

the Gilbarco VaporVac Vapor Recovery System. 

G-70-191 Healy/Franklin VP-1000 Vapor Pump Phase II Vapor Recovery System(Healy 

AA ORVR Phase II Vapor Recovery System)_. 

G-70-196 Certification of the Saber Technologies, LLC SaberVac VR Phase IT Vapor 

Recovery System 

G-70-199-AJ Certification of the Gasoline Dispensing Nozzles to the Liquid Retention of 3 50 

millileters per 1,000 Gallons Dispensed. 

VR-201-A Healy System Inc. Phase II Enhanced Vapor Recovery (EVR) System Not 

Including lSD 

EVR-202-A Healy Phase IT Enhanced Vapor Recovery System Including Veeder-Root lSD 

System 

G-70-204-A Certification of the Gilbarco VaporVac/OPW Vaporsaver ORVR-Compatible 

System 

(j) Department Adopted CARB Stage ll System Executive Orders for Above Ground 

Storage Tank Vapor Recovery Systems. 

r 

' 

~ Number l Description, 

r -·-···- -···-· --- ·- certific~i-;;~~f a Ph~~~ Vap~~ cov ry System fu~ Abovegro~d Storage 

1 G-70-1 02-A Tanks with less than 40,000 Gallons Capacity for Gasoline or 

Gasoline/Methanol Blended Fuels ' i . 

-G-70-116- F rc~n Vault Above~?und Tank V !il?_?r Recovery System. . I 

j ! . G-70-128 !Bryant Fuel Cell Aboveground Tank Vapor Recovery System 

--·G 7o-13"0"A ~aui0b~;i!~~~T~ Vapor Recov~ry_ Sy~~em·- - ·-----.---------·--' 

~-· G-70-131A .ITank Vault Ab~~~~ound Tank Vap~rRecovery System 

G-70-132-A jsupervault Aboveground Tank Vapor Recovery System 

G-70-132-B lsupervault Aboveground Tank_'\';f>; R~cov~· ~~~ .. 

~-·--···a::-io-=-i 36 IFireSafe Aboveground Tank Vapor Recovery System 

: - G-70-i 37 ----[F~e1Safe Aboveground Tank Vapor Recovery System -·----- ~---- . -·. . - -

.. 

I 

;Phase II Vapor Recovery Systems Installed on Gasoline Bulk 

jPlants/Dispensing Facilities with Aboveground ~anks _j -------r-~-------~--------~~~~~~-------------~~ 

G-70-138 

G-70-139 

1

1

Addition to the Certification ofthe Hirt Model VCS-200 Phase II Vapor 

Recovery System 

jintegral Phase I and--P--has_ e_II _A- b-ov_e_gr_o_un_ d_T_ank --C-o-'-nfi- 1-gur - ations with fue 

lHealy Phase II Vapor Recovery System -"' . 

r ! G-70-140-A 

\ G-70-142-B !Phase I Vapor Recovery System for Aboveground Gasiline Storage Tanks 

I ······-····-·-··-······· ... - ··----··-r---·-·-·--.. -- . - ··-'--- • ·:· - ----.. -------· --·--. 

G-70-143 WIT Vault Aboveground Tank Vapor Recovery System 

------ ----------------------~ 20 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

I 

0 _

70_147_A New United Motors Manuf~ctur~ng, Incorporated Phase II Vapor Recovery --

System at the Fremont, Cahforma Assembly Plant --- " . ·- . '-·. --- -- . ---- ...... - - -... --- - .. --- - . - . I . .9:? 0-~~~~ ~~?e ~~be. ~~<!vegr<?~nd Tank Vap~x Rec()very Sys~em ------------·-· 

I G-70-152 .. ~e~~!:~,~~~~~::;~ks and Manufacturing Aboveground Tank Vapor 

~- ---(}~70-15 5. !Petroleum Marketing Abov'~ground ank·V~p~r 'R~~ov~;ySy~~~--------.... ----- .... 

r-o-7o-Is6 .:_· E~~~it'A~~o~ct r;~k v ~~~~ -A:~-;~t v~'P~;Reco~~cy--sy;t~m -

r . G-70-1S7 JEcovault Ab~v~ground T;~B~i~~~ .. V~p~ R~~;,-;cy- syst~-- ..... . . M 

f .... ·G=70:1S8-A jFiresafe Abo~e~~~~d T~~k Vapor Recovery System .... r-·-------· - T-- .. -.. - . .. .. -- . . -------·------------.. ----------·-·-

. G-:::: :; .. ~::::,::~~!~ ¥~~i:~::P~:~~~~::~ ~~::;_-; ;-Ab-;;~~~;,d Ta;,i· -- Vapor Recovery System ··--··· ............... ---- -- ..... - ·--- ' - - - -- .... ... ......... •.. .. .. ....... . . . 

[ 70 16?._::~ -J~!~~J. .. :!'~ .. !.n.~tit~te ~~~e~ll:~~A~~~!ound Tank Vapor Recovery System --

'10-70-167 ~oVa\llt Aboveground Tank VaP.or Recovery System 

L - G-70-168 _IBry_~t~uel sx~t.~~s P~ase I Vap~~ R~~~~~ry ·y-~t~-;----- -------- ··- ----

·-~ ;0-1 ;~----T_H~sst~~h VCP-3A Vac~~Assist Phase rrv~p;; covery System for -- ---· 

I_ !Aboveground Tank Systems 

[ o-1o-1s1 ··. _ ~~~~~~~~~~~~~~~l~~~:~ uv~~~~~~sy~~f~ ---· 

~- · Healy Model400 ORVR VaporRecov. ery System for Aboveground Tank I v1 

v1 0 Systems 

I ~~-;90---""-'-!Guardia · C~n ai ent, Corporation Armor(:;;; Abovegr~~~d T;~'\rap;r ·· .. 

I !Recovery System 

---- ~~~ ;;; --- C~rtifitatio -- fth~ H~;iy M~del4oo ORVR N~z~l~ fo~ Existi~g 

. :Above~~oru:d Stora~~ Tal1k Systems ----------------------- ------.. -- ·--

[ 

Certification ofthe Hill-Vac Vapor Recovery System for Cargo Tank Motor 

G-70-

193 __ '! ~h.i.~!e :F.l1~ling Systen.:s 

-- ·-- ----------. Containment Solutions Hoover Vault Aboveground Tank Vapor Reco~ery

l_ G-70-19~ System ·· - ·- . .... ........ . . 

-~ ICretex Compani~·-'- s,;::.::.:.::.~=-..:::.c:::.: el..;;.:_;_; lt_; _; ro-'-un ank ___ -'-V- a_p_o_r_R_e_c...:. ov'-e-ry __ _ G-70-195 System 

[-o~7o i97-----· synchrotek F~~3 Ph~~ iTv~~~it~~~~cy-s;;;~ - · - · · 

r--=-G-70 2~~---- ldc~tl~ Ab~~~~~~;~d B~lo Gr de Fuel Vault with Bal~;~ Vap;r 

1.. !Recovery System and Buried Vapor Return Piping 

r:l ::.:..· _ __;.;__~ _ _;;; Oldcastle Abo~e~ound Bel~~ Grade F~el Vault with B~lance Vapor G-70-201 Recovery System and Trenched Vapor Return Piping 

;:....~------'-'· --:..., ld--'-'--'- st-le bov~gro~d Belo~-GradeFuel Vault with Gilb-~~~0 Vap~rVac -- G-70-202 

j 1Phase IT Recovery System and T~enched Vapor Return Piping 

(k) The provisions and requirements of 310 CMR 7.24 (6)(a) and (b) are subject to the 

21 
Stage II Final Amendments Redline/Strikeout Copy 12-01-08 

enforcement provisions specified in 310 CMR 7.52. 

22