## Stage II Final Amendments R edl i ne/S tri keout**opy ~**  

## 2-01-08
310 

### CMR 7.00 

### Definitions Isolate shall meanme ans, for the purposes of 310 CMR 7.24(6), to take out of service ef- one or more components of a Stage 

### ll system so that the remainder of the Stage 

### ll system operates as required by the terms and conditions of the system's currently applicable Executive Order. 

### Minor Modification s hall meanmeans , for the purposes of310 CMR 7.24(6) , the re-installation, repair or replacement of one or more Stage II System components that is not substantial, including , but not limited to: less than 50% of the motor vehicle fuel dispen sers (e.g., 1 of 4 dispensers); a central vacuum unit of a Healy 400 ORVR nozzle system or Healy 600 nozzle system; ball float extractor valve housings; dispenser mounted vapor pumps; or " screw-on " s pill or dry break buckets. If the re-installation, repair or replacement of Stage II System components occurs at a motor vehicle fuel dispensing facility with two or less dispensers, the re-installation, repair or replac ement of only one of the motor vehicle fuel dispensers shall be a Minor Modification. 

### Routine Maintenance sl 1all meanm eans , for the purposes of 310 CMR 7.24(6), the regular reinstallation, repair or replacement of one or more Stage II System components including, but not limited to: hoses; nozzles; breakaways; swive ls; hose retractors; bucket plow rings; "slip-on" spill or dry break buckets; 

### "0" rings and seals; s ubm ersib le pumps or suction pipes; fill adaptor s; fill tubes; vapor adaptors; 

### fill and vapor caps; drain valves; monitor caps; or riser caps. 

### Substantial Modification s h al l meanmeans, for the purposes of 310 CMR 7.24(6), the reinstallation, repair o r replacement of one or more Stage II System components including, but not limited to: 50% or more of the motor vehicle fuel dispensers (e.g., 2 of 4 dispensers ) ; the replacement of one type of Stage II system with another type (e.g., replacement of a balance system with a vacuum assist system, or a Healy 400 ORVR nozzl e system or Healy 600 nozzle system with a Healy VP-1 000 system); or the re-installation, repair or replacement of Stage II System components requiring excavat ion below a shear valve or tank pad (e.g., vapor return piping, vent piping, vapor space tie bar, two-point or coaxial Stage I systems; or motor vehicle fu el storage tanks). 

### If there-ins tallation, repair or replacement of one or more Stage II System components occurs at a motor vehicle fue l dispensing facility with two or fewer dispensers , the re-installation , repair or replacement of all motor vehicle fuel dispensers shall be a Substantial Modification. 310 CMR 7.24(6) U 

### DISPENSING

.QF MOTOR VEHICLE FUEL. 

### (a) Applicability and Installation Requirements 1. Any person who owns, leases, operates or contro l s a motor vehicle fuel dispensing facility constructed or substantially modified after November 1 , 1989 shall install , prior to commencing operation, a Stage II system as r equired by the terms and conditions of the system's currently applicable Executive

. Order and any Approval Letters issued by CARB on or be fore (THE EFFECTIVE DAJ E O F THE8E**i\MEl'1D~ffiNT8) March**  I, 2009 pursuant thereto. 2. Any per son who owns, leases, operates or controls a motor vehicle fuel dispen s ing fac ility constructed before November 1, 1989, that has not been substantially modified since November 1, 1989 shall install a Stage II system as required by the terms and conditions of the system's currently appl icabl e Execu tive Order_and as required by the following

## Stage II Final Amendments Re d line/Str i keout Copy 1 2 -01-08
schedule:

a. by April 1 , 1991 where the annual (calendar year) throughput of the motor vehicle fuel dispensing facility is greater than or equal to 1,000,000 gallons of motor vehicle fuel; or b. by April 1, 1992 where the annual (calendar year) throughput of the motor vehicle fuel dispensing facility is less than 1,000,000 ga,llons but greater than ot equal to 500,000 gallons of motor vehicle fuel; or

c. by April 1, 1993 where the annual (calendar year) throughput of the motor vehicle fuel dispensing facility is less than 500,000 gallons per year but is greater than or equal to 20,000 gallons in any one ca1ei1.dar month; or d.

. by April 1, 1994, or 90 days after dispensing 10,000 gallons or more in any calendar month, whichever is later, for all other motor vehicle fuel**d~spensing** facilities. 3. Any person who owns, leases, operates or controls a motor vehicle fuel dispensing facility c()nstructed before November 1, 1989, which has not been substantially modified since November 1, 1989 and which has not dispensed greater than 10,000 gallons of motor vehicle fuel in any one calendar month since January 1, 1988 shall maintain, on site at the facility, monthly records of the total number of gallons of motor vehicle fuel dispensed at said facility for the most recent rolling five year period. · 4. Any person who owns, leases, operates or controls a tank truck engaged in the direct dispensing of motor vehicle fuel to a motor vehicle or portable container shall install, by September 1, 1995 or prior to commencing operation, whichever is later ., a Stage II sys t em that meets the terms and conditions of the system's currently app licable Executive Order. Tank trucks dispensing motor vehicle fuel to emergency motor vehicles or portable containers during fire fighting activities or a declared emergency situation are exempt from the requirements of310 CMR 7.24(6). 5

. Any person subject to 310 CMR 7.24(6) shall conspicuously post S t age II system opera t ing instructions on both sides of all motor vehicle fuel dispensers or at a position adjacent to the di s pe n sers that is clec;rrly visible to the system
.operator during the refueling process. Such instructions shall include:

a. a clear pictorial or written description of how to correctly dispense motor vehicle fuel using the installed Stage II system; b. a warning not to cont inue di spensing motor vehicle fuel ("topping-off') after automatic sys t em shutoff has engaged; and

c. the telephone number of the Department's Stage IT Consumer Hotline. 6. Stationary motor vehicle fuel storage tanks used for following purposes only shall be exempt from the requirements of 310 CMR 7.24(6).
2

## Stage II Final Amendme nts Red line/Strikeout Copy 12-01-08

a. A stationary motor vehicle fue l storage tank of 550 gallo n s or less capacity, used for the purpose of fueling implements of husbandry , provided the fuel storage 

### tank is equipped with submerged fill pipes

. b. · A stationary motor vehicle fuel storage tank of grea t e r th an ?50 gallon s . but 1000 gallons or less capacity, used for the purpose of onsite fueling of motor vehicles with motor vehicle fuel that is the by-product of motor vehicle salvage yard operations, provided the fuel storage tank is equipped with:

1. a subme rged fill pipe; and

u . a press ure vacu um vent valve. Any person who owns, l eases, operates or contro l s a stationary motor vehicle fuel storage tank currently installed at a motor vehicle salvage yard and not in com pliance with the requirements of this subsection shall take such action as necessary to comply with the requirements of this subsection on or before ( 1 80 days of the effective d ate of these amen dments) September l

. 2009. 7. On or after (THE EFFECTIVE D ATE OF THES E AMENDMENTS) March 1. 2009, an y person who owns, lease s, operates or controls a new l y installed motor vehicle fuel dispen sing facility where a Stage II system is install ed in compliance with 310 CMR 7.24(6)(a) 1. shall install a pressure /v acuum 

### (PN) vent cap on each underground motor vehicle fuel s torage tank vent located at said facility, prior to commencing operation. Any person who own s, leases , operates or controls an existing motor vehicle fuel dispensing facility where a vapor balance Stage ll system is installed as of (THE EFFECTIVE DA TE OF TI lESE AMENDMffi'HS)March 1.' 2009 shall install a 

### PN vent cap on each underground motor vehicle fuel storage tank vent on or before said facility's first Annual In-U se Compliance Certification submittal due date after (THE EFFECTIVE D ATE OF THESE AMENDMENTS+ 30 days)Apr il 1. 2009

. EachPN ve nt cap shall maintain 3.0+ / -0.5 inches of water pre ss ure, and 8.0 +/

- 2. 0 inche s of vacuum. Note : Per the applicabl e CARB Executiv e O r ders. a bove gro und motor vehi c le fu e l stora ge tanks and a ll underground motor v ehi cle fuel storage tanks with v acu um assist tvpe Stag e II systems are a l so req uired to ha ve 

### P N vent caps. 

### (b) Operation and Maintenance Requirements 1. Any person subject to 310 CMR 7.24(6) shall comply with the following operation and maintenanc e requirements.

a. Operate and maintain the installed Stage II system as required by the terms and conditions of the system's currently applicable Executiv e Order. b. Take such actions as nece ss ary to comply with the applic able term s and conditions of any new or modified Executive Order upon Department re vision of 3 10 CMR 7.24(6) to incorporate su ch new or modified Exe cuti ve Ord er. Such act ions s hall be taken either :
1. during applicable Routine Maintenance , Minor Modification or Substantial Modification of the Stag e II Syst e m; or 3

## S ta ge II Final Amendments Redline/St rikeout C o py 12-01-08

u. within four years, whichever occurs first.

c. Once every seven (7) days perform a weekly visual inspection of the Stage II system components to determine if such components are installed, functioning and unbroken as required by the terms and conditions of the system's currently applicable Executive Order. Each visual inspection shall include, but not be limited to, inspection of: nozzle boots and splash/vapor guards; hoses; hose retractors, coaxial adaptors, dry breaks, fi ll caps and gaskets, vapor recovery caps and gaskets, spill containment boxes and drain valves. d. U pon determining a Stage II system component is incorrectly installed, nonfunctioning or broken during a visual inspection, immediately: i. repair such component(s) as required by the terms and conditions of the system's currently applicable· Executive Order; or ii. stop dispensing motor vehicle fue l thro u gh such component(s), conspicuous ly post "Out of Service" signs on s uch component, aud repair such component as required by the terms and conditions of the system's currently applicable Executive Order within 14 days of the date such component is determined to be incorrectly installed, non- functioning or broken.

e. 

## if an incorrec tly installed, non- functioning or broken component cannot be repaired as required by 310 CMR 7.24(6)(b) l.d. , such component shall inimediately be Isolated. "Out of Service" signs sha ll be conspicuously posted on sa id Isolated components until such time as said component areis correctly repaired as required by the Stage II system's currently applicab le Executive Order. 

### f. If an incorrect ly installed, non-functioning or broken component cannot be repaired or tsetatelsolated as required by 310 CMR 7 .24( 6)(b )_ l.d. or e., the facility owner/operator shall immediately stop dispensing motor vehicle fuel and conspicuously post "Out of Service" signs on all motor vehicle fuel dispensers until such ti me as all i ncorrectly installed, non-functioning or broken components are correctly repaired as required by the terms and conditions of the Stage II system's currently applicable Executive Order. 2. A visual inspection of a Stage II system to meet the requirements of 310 CMR 7.24(6)(b)l.c. shall be performed only by a person who is trained to operate and maintain the Stage II system as re quired by the terms and conditions of the system's curren tly applicable Executive Order. A current record of all persons trained shall be maintained on site or, fo r tank trucks, at the address from which the tank truck is principally operated, and shall include the following:

a. the date training was l ast received; b

. the trainee ' s printed name; and

c. the personal s i gnature of the trainee acknowledging receipt of the training

. 4

## Stage II Final Amendments Red line/Strikeout Copy 12-01-08

3. Any person subject to 310 CMR 7.24(6) shall maintain a ll Stage II system maintenance records on site, in a centralized location, for the most recent rolling twelvemonth per iod. Such records may be either (a) hard copy documents or (b) electronic documents, provided that a hard copy of the electronic documents shall be printed on-site immediately upon**reque~t.** Such maintenance records for tank trucks shall be maintained at the .address from which the tank tru ck is principally operated. Stage II system maintenance reco rd s shal l include:

a. all of the facility's weekly inspection c h eck l ists fo r the prior rolling twel vemonth period, identifying: i. the date each weekly visual inspection was performed and the signature of the person who performed the visual inspection; ii. any Stage II system componeht determined to be incorrectly instal led, non - functioning or broken;

m. whether the identified incorrectly install ed, non-functioning or broken component was immedi ately repaired, taken out of service and repaired within 14 days, I so lated, or the faci l ity stopped dispensing motor vehicle fuel and all fue l dispensers were taken out of service; iv. the date the incorrectly installed, non-functioning or broken component.B_ id entified in iii. a bove :waswe r e repaired. b. A copy of compliance testing company test results for all Stage II comp li ance tests during the prior rolling twe lve- m ont h period.

c. A copy of the Stage II system's most recent Annual In -Use Compliance Cert ific ation. 4. A ll records maintained pursuant to 3 1 0 CMR 7.24(6)(b) 2. and 3. shall be made avai lab l e to t h e Department or the US E PA immediately u pon requ est. In the event requested records cannot be made immediately available, requ ested records shall be delivered to the Department or the US EPA, as applicable, within 24 hours of the initial request. (c) Compliance Testing and Certification Requirements 1

. Stage 

### ll system testing, reco rd keeping and certification as a result of Routine Maintenance or Minor Modification of a Stage II system.

a. In the even t of Routine Mainten ance, a record of such maintenance shall be main tained in accordance w i th 310 CMR 7.24(6)(b) 3. Co mpl iance test in g and sub mitt al of a compliance c - ertification to the Department is not required

. b. In the event of a Minor Modification of a Stage II system, applicable comp li ance tests shall be performed and passed prior to commencing system operat i on and a record of such modification and test results shall be maintained in 5

## Stage II Final Amendmen t s Redlin e/S t r i ke o u t Copy 12-01-0 8
accordance with 310 CMR 7.24(6)(b) 3. Submittal of a compliance certification to the Department i s not required.

2. Installa t ion/Substantial Modification Certification. Any person subject to 310 CMR 7.24(6) who installs or makes a Substantial Modification to a Stage II system**after ~** **~G+WE-DATE OF---THE.£E...-ABN~-)March**  L 

### 2009 , shall,

.prior to commencing operation, perform and pass all applicable compliance tests pursuant to 310 CMR 7.24(6)(d). and submit to the Department within 7 days of performing and passing said tests, a fully completed and signed Installation/Substantial Modifica t ion Cettification, on a form obta ined from the Department, attesting to the following:

a. the installed or substantially modified Stage II system ts installed or substantially modified in compliance w ith 310 CMR 7 .24(6)(a); b. all applicable compliance tests as required by 310 CMR 7 .24( 6)(d) were performed and passed; and

c. t he ap p licable installation compl iance tests were performed and passed not more than 30 day s pt io r to th e date p os t ma r ked on the envelope used to submit the Certification to the Dep attmen t. · 3. Annual In-Use Compliance Certification. Except as provided in 3 10 CMR 7 .2 4(6)(c)**L** 

### any person subject to 310 CMR 7.24(6) shall annually submit to the Department a fully completed and signed Annual In-Use Compliance Certification, on a form obtained from the Department, attesting to the following:

a. the installed Stage II system is operated and maintained as required by 310 CMR 7.24(6)(b); b. the following in-use compliance tests, as applicable, were . Performed as required 

### by 310 CMR 7.24(6)(d): i. Vapor balance systems. Annual in-use compliance**test~:** 

### Pressure Decay Test; Vapor-Tie Test; 

### PN Vent Test. Every

- third

-year in-use compliance test: Dynamic Pressure/Liquid Blockage Test. · ii

. Vacuu m assist systems. Annual in-use compliance tests: Pressure Decay Test; Vapor-Tie Test; 

### PN Vent Test; and Air-to-Liquid Ratio Test. E very-third-year in-use compliance test: Dynamic Pressure/Liquid Blockage Test.

111. 

### Healy systems. All applicable tests shall be performed annually.

c. The applicable in-use compliance tests were performed and were-passed not 6

## Stage II Fina l Amendments Redline/Strikeout Copy . 12-01-08

more than 30 days prior to the date postmarked on the envelope used to submit the Certification to the Department. 4. Alternative Annual In-Use Comp l iance Certification. Any person subject to 310 CMR 7.24(6) who submits two consecutive years of Annual In-Use Compliance Certifications**~H FStta** **fl:He in**  compliance with 3 1 0 CMR 7.24(6)(c) 3. in which all applicable in-use compliance tests were passed on the first try, as certified 

### te as requ ire4-9y-pursuant to 310 CMR 7.24(6)(g)8., may elect to submit annually to the Department an Alternative Annual In

- Use Compli ance Cert i fication on a form obtained from the Department:

a. Facilities meeting the requirements of310 CMR 7.24(6)(c) 4. and electing to submit an A lternative Annua l In-Use Compl iance Certification shall be: i. exempt from annual Stage II compliance testing requirements in the year following the submittal of two consecutive years' of Annual In-Use Compliance Certifications in comp liance with 310 CMR 7.24(6)(c) 4.; and ii. subject to all applicable Stage II compliance tests as refe r enced in 310 CMR 7.24(6)(d) in the second year following the submittal of two consecutive years' Annual In-Use Compliance Certifica ti ons in compliance with 310 CMR 7.24(6)(c) 3., and every other year thereafter. b. Any person submitting an Alternative Annual In-Use Compliance C e rtificati o n to the Department shall fully comp lete and sign said Certification and attest to the following: i. the installed S t age II system is correctly operated and maintained as required by 31 0 CMR 7
. 2 4 ( 6)(b); i i

. all applicable compliance tests were performed and passed as required by 310 CMR 7.24(6)(c) 4

. a.ii., and

11 1. The applicable compliance tests were performed and were passed not more than 30 days p rior to the d ate postmarked on the envelope used to su b mi t the Certification to t he Department.

c. Any person submitting an A l ternative Annual In-Use Compliance Certification and fai l s one or mo re comp l iance cert ification tests on the first try as required by 310 CMR 7.24(6)(c) 4. shall be required, in subsequent years , to annually certify in compliance w i th the requirements of 310 CMR 7.24(6)(c) 3., until s u ch time as #iesaid person meets the requirements in 31 0 CMR 7 .24(6)(c) 4. 5. Annual In-Use Compliance Certification Submittal Requirements. The annual submitta l d ate for Certificatio n s required pursuant to 310 CMR 7.24(6)(c) 3. and 4., is no later than :

a . For persons subject to 310 CMR 7.24(6) who install or make a Substantial Modi fication to a Stage II system on or after J anuary 1, 200 1 , the anniversary of the 7

## S ta ge II Final Amendments Redline/Strikeout Copy 12 - 01 -08
date postmarked on the envelope used to submit to the Department the Installation Comp l iance Certification required by 310 CMR 7 .24(6)( c) 

### 1. or the date the facility commenced operation, whichever occurs first; and b. For all other persons subject to 310 CMR 7.24(6), May 1, 2002, or a date otherwise provided by the Department, whichever is earlier. Persons subject to 310 CMR 7.24(6)(c) 5.b. who are provided an annual submittal date by the Department shall be notified by the Department of their first annual submittal date and ·required in-use compliance tests pursuant to 310 CMR 7.24(6)(c) 3.b

. no less than 90 days prior to the first annual submitta l date established by the Department.

c. Upon request of any person subject to 310 CMR 7.24(6), the Department may revise said person's annual Certification submittal date. Such revision shal l set a revised annual submittal date that is no more than 12 months after the otherwise applicable submjtta l date. 6. Any person who owns, le ases, operates or controls a Stage II system that fails one or more in-use compliance tests required by 3 10 CMR 7.24(6)-t @ 3.:. or 4., shall immediately:

a. repair incorrectly instal led, non- functioning or broken component as required by the terms and conditions of the Stage II system's currently applicable Execut ive Order; b. re-test and pass each failed test; and

c. submit to the Department the required Annual In-Use Compliance Certification on or before the facility's Annual In-Use Compliance Certification submittal date or within 30 days of the date of the Stage II**system~s** 

### first passing test result as required by 310 CMR 7
. 24(6)(c) 3.c. or 310 CMR 7.24(6)(c) 4.c., as applicable, whichever occurs first. 7. If a facility fails one or more required in-use compliance tests and the incorrectly installed, non- functioning or broken components cannot be repaired as required by 310 CMR 7.24(6)(c) 7
. , the facility owner/operator shall. immediately:

a. i-se-1-a:tei solate the incorrectly installed, non-functioning or broken components from the Stage II system so that the remainder of the Stage ll system operates as required by the terms and conditions of the system's currently applicable Executive Order; and b. submit to the Department the required Annual In-Use Compliance Certification based on passing test results for the remainder of the Stage II system on or before the facility's Annual In-Use Compliance Certification submittal date or within 30 days of the date of the Stage II system's first passing test result as required by 310 CMR 7.24(6)(c) 3.c. or 310 CMR 7.24(6)(c) 4.c., as applicable, which ever occurs fi r st.

c . Any Stage II system component Isolated from the remainder of the Stage ll System shall remain I solated i.mtil such time as: 8

# · I Stage II Final Amendments Redline/Strikeo ut Copy 12-01-08

i. said component is repaired as required by the terms and conditions of the Stage II System's currently applicable Executive Order; and ii. all applicable , compliance testing, record keeping and certification requirements for the Routine Maintenanc e, Minor Modification, or Substantial Modification of a Stage II system are complied with. 8. If 

### a facility fails one or more required in-use compliance tests and the incorrectly installed , non-functioning or broken Stage II system component cannot be repaired as required by 310 CMR 7 .24(6)( c) 6. or 7 ., the facility owner/operator shall immediately stop dispensing motor vehic le fuel and conspicuously post " Out of Service " signs on all motor vehicle fuel dispensers until such time as:
a. all incorrectly installed , non-functioning or broken components are repaired as required by th e terms and conditions of the Stage II sys tem' s currently applicable Executive Orde r ; b. all applicable in-use compliance tests are performed and passed as required by 310 CMR 7.24(6)(c) 3. or 4., as applicable; and

c. a fully completed Annual In-Use Compliance Certification has been submitted to the Department as required by 310 CMR 7 .24( 6)( c) 3. d. If 

### a facility fails one o r more r e quired in-use compliance tests and is subject to 310 CMR 7.24(6)(c) 8., for purpose s of compliance with the Annual In-Use Compliance Certification submittal requirements of 31 0 CMR 7 .24( 6)( c) 3. or 4., said facility owner/operator s hall submit to the Department a fully co mpleted and signed Stage II System Closure No tificati on as required by 310 CMR 7 .24( 6)( e) 2. on or before sai d facility 's currently applicable Annual In-Use Compliance Certification submittal due date. 9. Any Certification submitted to the Department as required by 31 0 CMR 7 .24(6)( c) shall be s igned by a Stage II System Responsible Official as required by 310 CMR 7.24(6)(£). 10. Any person subject to 310 CMR 7.24(6 ), upon written notice from the Department, s hall perform such compliance tests as the D e partment determines necessary to demonstrate the Stage II system is in stalled and maintained as required by the terms and conditions of the system's currently applicable Executive Order and s hall submit the results to the Department within 14 days of the performance of sa id tests
. (d) Stage II System Compliance Testing Requirements 

### For the purposes of 3 10 CMR 7 .24( 6)( c), the following Stage II System compliance tes ts and requirements shall be required: 1 . Vapor Balance sys tems. Pressure Decay Test, Vapor-Tie Test, 

### P N Vent Test and Dynamic Pressure/Liquid Blockage Test 9

## Stag e II Final Amendments Redline/ Strikeout Copy 12 -01 - 08

2. Vacuwn Assist systems. Pressure Decay Test, Vapor-Tie Test, 

### PN Vent Test, Air-to-Liquid Ratio Test and Dynamic Pressure/ Liquid Blockage Test 3. Healy systems. a. Healy 400 ORVR (Executive Order # G-70-186) , Healy 400 ORVR Above Ground Storage System (Executive Order # G-70-187) and Franzen-Hill Cargo Tank Truck System (Execut i ve Order # G

- 70-193): Pressure Decay Test: Vapor Tie Test; 

### PN Vent Test; Exhibit 4: Vapor Return Line Vacuum Integrity Test; and Exhibit 5: Fillneck Vapor Pressure Regulation Fueling Test. b. Healy 600 (Executive Order # G-70 -165 ): Pressure Decay Test ; Vapor Tie Test; 

### PN Vent Test; Air-to-Liquid Ratio Test ; and Exhibit 4: Vapor Return Line Vacuum Integrity Test. 4. Compliance tests performed to meet the requirements of 310 CMR 7.24(6)(c) shall be performed only by a person or Stage ll compliance testing company . that has submitted to the Department a Stage II Compliance Testing Company Notification as required by 3 1 0 CMR 7 .24( 6)(g) 1. (e) Notification Requirements. 1. Any person, upon entering into a purchase, lease or other contractual agreement by which said person becomes the owner, operator, lessee or controller of an existing motor vehicle fuel dispensing facility or tank truck subject to 310 CMR 7.24(6) shall submit to the Department, within 30 days of the effective date of becoming such an owner, operator , lessee or controller or within 10 days of a written request from the Department, a fully completed New Stage 

### ll System Owner, Operator, Lessee or Controller Notification on a form obtained from the Department.

a. 

### +ReSaid Notification shall include the following: 

### i. the name of the new Stage II system owner, operator, lessee or controller and related business documentation, including the name and address of the facility w here the Stage ll system i.s located or from which the tank truck is principally operated; and

11. the 

### effective date sa id person became the new 

### owner, operator , lessee or controller. b. 

### A&ySaid Notification shall be sig ned by the individual who is a Responsible Official for the new owner, operator, le ssee or controller regarding the Stage II 10

## Stage II Final Amendments Redline/Strikeout C opy 12-01-08 system , who shall attest to the following: 

### i. I certify that I personally examined the foregoing and am familiar with the information contained in this document and all the attachments and that, based on my inquiry of those persons inunediately responsible for obtaining the information, 

### I believe that the information is true, accurate and complete. 

### I am aware that there are significant penalties for submitting false information, including possible 

### fmes and imprisorunent; ii. 

### I am fully authorized to make this attestation on behalf of this faci li ty or tank truck, as applicable.

2. Any person subject to 31 0 CMR 7 .24(6), upon entering into a sal e, lease or other contractual agreement by which said person relinquishes his

. or her authority as an owner, operator, le ssee or controller of a facility or tank truck subject to 310 CMR 7.24(6), shall submit to the Department, within 30 days of the effe ctive date of said sale, lease or other contractual agreement, a signed letter notifying the D epartment of the following:

a. the name of the

. person relinquishing his or her authority as an owner, operator, lessee or controller of the facility or tank truck subject to 310 CM R 7.24(6) , the facility name , Stage II Fac ilit y 

### Customer Code N wnberDEP Fac ilitv Account Ntm1 b e r and address or the address from which the tank truck is principally operated, as applicable; b. the name of the new owner, operator, lessee or controller of the facility or tank truck subject to 310 CMR 7.24(6) and related business information, including the new facility name and address or the address from w hich the tank truck is principally operated, as applicable; and

c. the effective date of the change of owner , operator, lessee or controller

. 3. Any per son subject to the requirements of 31 0 CMR 7 .24( 6) seeking to permanently or temporarily take out of use an exist ing motor vehicle fuel dispensing facility or tank truck shall submit to the Department a fully completed and signed Stage 

### ll System Closure Notification, on a form obtained from the Department.

a. Said Notification s hall include the following: i. the name of the Stage II facility owner, operator, lessee or contro ller and related busin ess inform ation, including the name and addres s of the facility where the Stage 

### II system was located or from which the tank truck was principally operated, as applicab l e; ii. the 

### Stage-H-f "U ei l#:y-GI:Jstem e:F-tea e -fl.tlflffieF DEP Faci lity A ccount N umbe r for the applicable facility or tank truck; and

111. a fu lly complete d N etifieatiet r-For Storage Ta n Jcs**Reg~E~'** 527 C MR 9
. 00 ( FP 2 90) F offil, as**ss ~eal-Fi;:e--f}e~aftfl-1~1ft,**  11

## Stag e II Final Amendm ents Redline/S trikeo ut C o py 12-01-08
OO €Bfflentffig that the**ap~le-fue-i -tfl:l€k** **-- is** **ei:ther** 

### permane ntly**e-t~-ake-H:-&l:lt-ef- 1:15e:-a**  copy of the Notification For Removal or C losure of In Place Underground Storage Tanks Regulated Under 527 CMR 9.00 CFP-290R) Form, documenting the permanent or tempormy out of use status of said facility or tank truck on record with the Massachusetts Department of Fire Safet y . b

. The temporary out of use status of a motor vehicle 

### fuel dispensing system shall be renewed as necessary by any person subject to the requirements of 31 0 CMR 7.24(6) by submitting a new, fhllv completed Stage II System Closur e Notification, on or before the annual · anniversaty of the effective date said dispens ing system was taken out of use, as noted in the required. FP-290R Form
. Said renewal shall include a cmrent FP-290R Form for said dispensing system on record with the Massachusetts Department of Fire Safety documenting the

·system ' s continued temporary out of use status
.**Aa:y:--'f:~er son**  subject to tHe R-"'Eftti-fe.m:€ftts o f 310 C MR 7 .2 1(6) ·. vho t emporarily take s out of use a Ft.letet: v ehicl e fuel dis pen sing**facil ty-s-lT&l~r-tB-re**  commencing the distribution of mot or vehicle fuet,perffiFm-aad-pass-aH-applicabl e co mp lian ce tests and subm it-to the**Dep~llly** coffil*eted Install ation/Substantial 

### M offifi: ea tiBn Gerfi.fieattan

- afl-fe£ttt.ire<4 by 310 CMR**24(61fcj-h- ~em~** **sl.:ia.J.~** be**reRe-~ec~g-aR-~fully** 

### comp leted In stallati on/Substantial 

### Med-i.fi:e.atien-Cer#.fi:catie&,---efl---Of'-befure the annual anniver sary**~he** date the loc al Fire Department signed the requir-ed FP 290 F01 m .**~enev•al-sltttl- l--i:nelOO.e-a--&Ufren-t--FP~r** **m,** as issued by the local Fife Depaflffient, 

### docum:en:tiflt:,'-the-fac.i:l:iifs-c

- em im red-temp<:tffiry out of use**st~**

c. Anv person sub j ect to the requirements of 310 CMR 7.24(6) who t emporarily takes out of use a motor vehicle fuel dispensing system shall. prior to co mmencing the distribution of motor vehicle fuel. perform and pass all .@.plicable compliance tests a11d submit to the Department a fully completed Installation/Substantial Modification Ce1tification as required by 3l0 CMR 7 .?4( 

### 6 )(c) 2

. cQ.. Any person subject to the requirements of 310 CMR 7.24(6), where the motor vehicle fuel dispensing facility is e#lier- permanently 

### or temporarily taken out of use, shall no longer be sub ject to 310 CMR 7 .24( 6) as of the effective date the faci lity was pe1manently t aken out of serviceuse as referenced in the required 

### FP290B, Form. 4. Any Notificat ion submitted to the Department as required b y 310 CMR 7.24(6)(e) shall be signed by a Stage II System Responsible Official as required by 310 CMR 7.24(6)(f). 

### (f) Stage II Sys t em Responsible Official Certification of Compliance. 1. Except in circumstances described in 310 CMR 7.24(6)(f) 2. , any Certification or Notification required by 310 CMR 7.24(6)(c) or (e) shall be signed by an individual who is · a Responsible Offic i al regarding Stage II system compliance.
12

## Stage II Fina l Amendmen t s R edline/S trikeout C opy 12-01-08
2. For S t age II systems owned by one party and leased, operated or controlled by another independent party and where both parties have separate Stage II compliance responsibilities, any Certification or Notification submitted in compliance with the requir ements of 310 CMR 7
. 24(6)(c) or (e) shall be signed by Responsib l e Officials for each p arty regard i n g Stage II system compliance. Each Stage II System Responsible Offici al s h all attest to the following: i. I certify that I personally examined the foregoing and am familiar with the informati on conta ined in thi s doc ument and all the attaclunents and that, based on my inquiry of those persons immediatel y responsible for obtaining the information , I 

### believe that the informa tion is true, accurate and complete. I am aware that there are s ignificant penalties for submitting false information, including possible fines and impr i sonment; ii.**~hat** 

### systems to maintain compliance are in place at the facility or , if applicable, at the location from which the tank truck is principally operated and will be maintained for the coming year even if the processes or operating procedures are changed over the course of the year; and

111. 

### I am ful ly authorized to make this attestation on behalf of this facility or tank truck, as applicable. 3

. Any p erson immediately responsible for o btaining information referenced in 31 0 CMR 7.24(6)(±), who knowingly and willfully makes false , inaccurate, incomplete or misleading statements purs u ant to any Certification o r Notification required under 310 CMR 7 .24(6), may be in vio l ation of 31 0 CMR 7 .24( 6). Not wi th standing the previous sen t ence, any per son subject to th e requir ements of 3 10 CMR 7.24(6), shall comply with al l app licab l e provision s of 310 CMR 7 .24(6). C o mpliance Testing Company Requirements 

### L On or after fR.J.E**EF FE** **CH¥E- M+E-GF-+I4ESE-A** **MENDMEN~ Mru:ch**  

### 1, 2009, any person who owns, leases, operates or contro l s a company that performs Stage II compliance tests to meet the r equirements of 310 CMR 7 .24(6)( c) shall submit to the Department a fully completed Stage II Compliance Testing Company Notification, on a form obtained from the Department, pr ior to performing any required Stage II compliance tes t.

a. the Notification shall include the following: i. 

### the name and business mail ing address of the Stage II compl i ance testing company owner, operator, lessee or controller; ii: the name and address of any business that is engaged in the in stallatio n o r Su b stanti al M odifica t i o n of Stage II systems and i s owned, o p erated, lease d o r controlled by, or affiliated w ith the owner, operator, lessee or contro ll er of the compliance testing company;
m. the name and address of any mo t or vehicle fuel dispensing facility o r 

### tank truck sub ject to 3 1 0 CMR 7
. 24(6 ) that is owned, operated, leased or 13

## Stage I I Final Amend ments Red lin e/ St r i keout Cop y 1 2-01-08
controlled by, or affiliated with the owner, operator, lessee or controller of the compliance testing company; 1v. the address and telephone number of the facility(ies) from which the daily compliance testing activities of the co mpli ance testing company originate and at which any reco rd s required by 31 0 CM R 7 .24( 6)(g) 10. are maintained;

v. a written description of the emp lo yee training systems in place at th e compliance testing company to ensure require d compliance tests are performed as required ·by applicable protocols and procedures , pursuant to 310 C MR 7.24(6)(g)6. and 7; and vi. a li st of all Comp liance Testing Company Re sponsible Officials with the authority to s ign Compl iance Tes ting Company Certifications on behalf of the co mpliance testing co mpan y. b. Each Notifi cat i on shall be s igned by an individual who is a Respon s ible Offi cial regarding the compliance tes ting company, . who shall attest to the followin g: i. 

### I certify that 

### I per s onally examined the foregoing and am familiar with the information contained in this document and all the attachments and that, based on m y inquiry of those persons imm e diately responsible for obtai ning the information , I believe that the information is true , accurate and complete

. I am a ware that there are s i gnificant p en alti es for s ubmitting false information, including possib le fines and impri so nment ;
11. Employee trai ning systems are in place at the company to ensure Stage 

### IT compliance tests are performed as required by all applicabl e protocols and procedures and s uch training systems will be maintaine d for the coming year**ev~n** if the protocols and procedures are changed over the course of the year; and

111. 

### I am fully authorized to make this attestation o n behalf of this Stage 

### IT Compliance Testing sC ompany. 2. Any person s ubject to the requirements of 3 10 CMR 7.24(6)(g) s hall no ti fy th e Department in writing of any change to the informati on submitted to the Department pursuant to · 310 CMR 7 .24 ( 6)(g) 1. within 14 days of the effective date of such change. Upon the Departme nt 's written request , the person shall submit a fully revised and completed Notification t o the Department as required by the requirements of 310 CMR 

### 7 .24(6)(g) 1. 3. No p erson subject to 3 1 0 CMR 7.24(6)(g) s hall perform any Stage IT compliance test unless sai d person has first been trained in accordance with the applicable compliance test p rotoco l s and procedures required by 310 CMR 7.24(6)(g) 6. and 7. 4. Any person subject to the requir em ents of 3 10 CMR 7
. 24(6)(g) s hall s ubmit , at l eas t 14

## Stage I I Fi na l Amendme nts Red li ne/S trikeo ut Copy 12-01-08

once every two weeks, a written list to the Department iden tifying all motor vehicle fuel dispensing facilities and tank trucks at which the company is scheduled to perform required Stage II compliance te s t( s) over th e next 14 day period.

a. The list shall be organized by Department region and date, and shall include the name and address o f each facility or tank truck to be tested, the applicable section under 310 CMR 7
. 24(6)(c)

- l-2_., 

### 2-J., or 

### ;4 ., the require d compliance tests sha±lt o be performed, and the estimated time that the company expects to arrive at the facility location. b. The D epartment shall be notified , in wri ting, of any change of date of an individual facility's schedul ed compliance tests no later than 9a.m. of the day the scheduled test(s) is to occur. Additions to a s ubmitted com pliance-tes ting schedul e s hall be su bmitted to th e Department, in writing, no less than two working days prior to the date of any scheduled test.

c. Failure to co mply with the Notific ation requirements of310 CMR 7.24(6)(g) 4. may be a bas i s for the Department to d etermine that tests conducted after inadequate notice are invalid. 5 Any person subj ect to the requirements of 310 CMR 7.24(6)(g) shall immedi ately notify the Department of any failed Stage II compliance tests performed as required by 31 0 CMR 7 .24( 6)( c) if said person did not return to retest the Stage II sys tem as required by 3 1 0 CMR 7.24(6)(c) 6. or 7. on or be fore the facility's Annual In -Use C omplian ce Certification submittal date , or within 30 da ys of the date of the Stage II system's first passing test result, which ever occurs first. Said per son shall notify the Department regarding the name and address of the fac ility , and the fac ility 's Facility Account Number

. 6. Any person subject to 3 1 0 CMR 7.24(6)(g) shall perform compliance tests to meet the requirements of310 CMR 7.24(6)(c) only upon confirmation that:

a. al l above gro und Stage II system components inc luding, but not limited to:**dispen se** **rs~ no** **zz es~** **swivels~** hos e retractors; hoses;**breakaways~** vapor check valves; and the pressure/vacuum valve(s) are in s talled as required and are the correc t components as required b y the terms and condit io ns of the system's curre n tly applicable Executive Order ; and b. all motor vehicle fuel dispen si ng facilities with two or m ore motor vehicle fuel storage 

### tanks are proper ly manifolded as required by the terms and conditions of the system's c urrently applicab l e Executive Order. 7. Any person sub j ect to 310 CMR 7.24(6)(g), shal l perform Stage II co mpli ance te sts to m eet the r equirements of 3 10 CMR 7.24(6) only in accordance with the applicable CalifOrni a Air R e sources B o ard test procedures cited qelow:

a. Pressure Decay Test (Bay Area Air Pollution Control Di str ict Source Test Procedure ST-30 (2/6/ 1 991)) and Tabl e A. Minimum Allowable Pre ssure. 

## I Table A

. M I N IM UM ALLOWABLE PRESSURE (Based on an initial pressure of 1 0.0" we.) 15

## Stage II Final Amendments Redline/St rik eo ut 

## Copy 12-0 1-08 Ullage Minimum Allowable Ullage M inimum Allowable (Ga l) Pressure ("we) (Gal) · Pressure ("we) 500 3.70 6 , 000 9
. 38 600 4

. 50 7 000 9.46 700 5

.20 7,500 9.50 800 5.80 8 000 9.52 900 6.20 9 , 000 9.56 1,000 6.50 1 0,000 9.60 1 , 250 7.05 11,000 9.62 1 ,7 50 7.90 12,000 9.64 2,000 8.20 13,000 9
. 66 2,250 8.35 14 , 000 9
. 68 2,500 8.50 1 5,000 9.70 2,750 . 8

. 60 1 6,000 9.71 3 , 000 8.70 17,000 9 .7 1 3,250 8

. 80 18,000 9.72 3,500 8.90 19,000 9.73 3 ,7 50 9.00 20,000 9
. 73 4,000 9
. 10 21,000 9.74 4,250 9.15 22,000 9
. 75 4,500 9.20 23,000 9.75 4,750 9.25 24 , 000 9.76 5,000 9.30 25 , 000 9.77 30,000 9.80 Note: For a valid test, total ullage must be at**e~t** 500 gallons but no more than 30,000 gallons. 

### b. Underground Piping Check (Vapor Tie) Test (San Diego County Air Po llution Contro l D i str ict Test Procedure TP

- 96- 1 , Section 5. 1. 9)

c. PressureNacuum Vent Test (Leak Rate and Cracking Pressure of PressureNacuum Vent Valves, CARB TP-201.1E) 

### PN reliefvents shall be tested to be within .29oz/in 2 

### or 0.5 inches of water co lumn of the desig ned pressure and within 1.2oz/in2 or 2.0 inches of water column of the vacuum settings. d. Air-to -L iquid Volume Ratio Test (C ARB 

### TP-201.5).

e. Dynamic Pressure/Liquid Blockage Test ( CARB 

### TP

- 201.4).

f. 

### Healy 400 ORVR (Execut i ve Order # G-70-186), Healy 400 ORVR Above Ground Storage System (Executive Order # G

- 70-187) and Franzen-Hill Cargo Tank T ruck System (Executive Order # G

- 70

- 193) Exhibit 4: Vapor Return Li ne Vacuum Integrity Test Exhibit 5: Fillneck Vapor Pressure Regulation Fueling Test Healy 600 (Executive Order 

### # G-70- 1 65) Exhibit 4: Vapor Return Line Vacuum Integrity Test. 8. Any 

### person subject to 310 CMR 7.24(6)(g) shall certify to the Department that each 16

## Stag · e II Final Amendments R edline/ S t rikeout C o py 12-01-08 compliance test performed to meet the requirements of 310 CMR 7 .24( 6)(c) was performed as required by 310 CMR 7.24(6)(g) 6. and 7.**~+ifeeA s**  

### app licable. the Certification shall be submitted on the applieahleg Stage II Installation/Substa nti al 

### Modific ation Certification or Annual In-Use Compliance Certification_

. as applicable. The**requir~d** 

### Certificationand · shall include:

a. the date each compliance test was frrst performed and the result; and b. the date each compliance test was performed and passed.

c. a notation whether, (i) the entire installed Stage II system was tested and passed all applicable compliance tested or (ii) incorrectly installed, non-functioning or broken components were Isolated from the remainder of the in stalled Stage 

# n system and the remainder · of Stage II system was tested and passed all applicable compliance tests. d. If the remainder of the Stage II system was test ed and passed all applicable compliance tests, as noted in 310 CMR 7 .24(6)(g) 8.c. , identify all components Isolated from the remainder of the Stage II system. 9. Each Certification submitted pursuant to 310 CMR 7.24(6)(g) 8. shall be fully completed and signed by a Compliance Testing Company Responsible Official, who shall attest to the following:

a. I certify that I personally examined the foregoing and am familiar with the information contained in this document and all the attachments and that, based on my inquiry of those persons immediately responsible for obtaining the information, I believe that the information is true, accurate and comp lete. I am aware that there are significant penalties for submitting false information, including possible fines and imprisonment; and b. I am fully authorized to make this attestation on behalf of this Stage II Compliance Testing c Company.
10. · Any person subject to 310 CMR 7.24(6)(g) shall maintain the following records on**site ~**  

### fo r a minimum of five years , at the location(s) referenced on the form submitted pursuantto310CMR 7.24(6)(g) l.a.iv:

a. A complete set of records of compliance tests performed to meet the requirements of3 10 CMR 7.24(6)(c). Such records shall include, by facility address :
1. 

### the date and first result for each required test performed;

n. the date each test was performed and passed; and

111. 

### an itemized list of all Stage II system components re-installed, repaired or replaced as necessary for the system to pass the applicable test(s).
17

## S tage II Final Amendments Redline/Strikeout Copy 1 2 -01 - 08
b

. A current record of all p ersons or employees trained as required by 310 CMR 7.24(6)(g)3. Such r eco rd shall**inch.~de** 

### the following: i. the date training was received; ii. the person or emp loyee's p rinted name; and iii. the personal signature of the person or employee acknow ledging receipt ofrequired training

. 11. All records maintained pursuant to 3 1 0 CMR 7.24(6)(g) 1 0. shall be made available to the Department or the US EPA inunediately upon the request of either

. (h) Violations of310 CMR 7.24(6) 

### For any person subject to 310 CMR 7.24(6) it shal l be a violation of310 CMR 7.24(6) to: 1 . 

### fail to submit any Certificat ion or Notification required by to 310 CMR 7 .24(6) as applicable; 2. make any false, inaccurate, incomplete or misleading $tatements in any Certification or Notification required by to 310 CMR 7 .24(6); 3. make any false, inaccurate, incomplete or misleading sta tements in any record, report, plan, file, log or register which said person is required to keep pursuant to 310 CMR 7.24(6); 4

. ho ld themselves out as a responsible official in v iolation of the applicable · requirements ofto 310 CMR 7.24(6); 5. fail to comp ly with any app l icab le standards imposed under 310 CMR 7.24(6); or 6. violate any other provision of 3 1 0 CMR 7 .24(6). (i) Department Adopted CARB Stage II System Executive Orders . Number Desc ription 

### G-70

- 7

- AD Certification of the Hasstech Model VCP-2 and VCP 2A Phase II Vapor Recovery System. G-70

- 14-AA Recertification of Red J acket Aspirator Assist Phase II Vapor Recovery System. G-70-17-AD Modification of Certification of the Emco Wheaton Balarice Phase II Vapor Recovery System. G-70-18-C Modification of Certification of the Shell Model 75B1 and 75B1-R3 Service Station Phase II Vapor Recovery System

. G-70

- 23

-AC Recertification of the Exxon Balance Phase II Vapor Recovery
. System. G-70-25-AA Recertification of the Atlantic Richfie ld Balance Phase II Vapor Recovery System

. G-70-33-AB Certification of the Modified Hirt VCS

- 200 Vacuum Ass i st Phase IT Vapor Recovery System. G-70-36-AD Modification of Certification of the OPW Ba lance Phase TI Vapor Recovery System. G-70-37-B Modification of the Certification of the Chevron Balance Phase II Vapor Recovery Sys tem with OPW nozzles for Service. 18

## Stage II Final Amendments Re dline/Stri k eo ut Copy 12-01-08
G-70-38-AB Recertifi cation of the Texaco Balance Phase II Vapor Rec o very System. G-70-48

- AA Recertification of the Mob il Oil Balance Ph ase II Vapo r Rec overy Syste m . G-70-49-AA Recertific atio n of the Uni o n Balance Phase II Vapor Recov ery Syste m . G-70-52·AM Certification of Components for Red Jacket, Hirt and Balanc e Phase II V apor Recovery Sys tem
. G-70-53-AA Recertification of the C hevron Bal ance Phase ll Vapo r Reco very System. G- 70-77 Certi fic ation o f the OPW Repair/Rep lacem ent Parts and Modification of the Cert ifi cation o f the Ol>W Balance Ph ase II Vapor Recovery System. G-70-78 Certific ation of the E-Z Flo N ozzl e Company R ebuilt Vapor Recovery Nozzles and Va p or R ecovery Components. G-70-101-B Certification of the E

- Z Flo Model 300 6 and 30 0 7 Vapor Recovery Nozzles and U se of E-Z F lo Compo nen ts wi t h OPW Mode l s. 11 VC and 11 VE Vapor Recovery Nozzles. G-70 -10 7 Certification of Rainbow P etroleum Products Model RA3003, RA3005, RA3006 and RA 3007 Vapor Recovery Nozzles and Vapor Recov ery C ompone nts. G-70-110 Certification of Stage I and ll Vapor Recovery Systems for Methanol Fue ling Facilities. G-70-118

- AB Certifi cation of Amoco V -1 Vapor Recovery System. G-70-125

-AA Mod ific ation of the Certification of the Husky Mode l V Phase II Balance Vapor Recovery Nozzle. G-70-127 Cert ifica ti on of the OPW Model 1 11- V Phase Vap or Reco very Nozzl e. G-70 -1 34 Cert ific ation of the EZ Flo Rebuil t A-4000 Series and llV-Series Vapor Recovery Sys t em . G-70

- 139 Add ition to the Certificatio n o f the Hirt Mode l VCS -200 Phase II Vapor Recovery System. G-70-150-AE Modification of the Certification of the Gilb arco VaporVac Phase ll Vapor Recovery System

. G-70-153-AD Modification to the Certifica tio n of the Dress e r / Wayne WayneVac Phase ll Vapor R ecovery Syst em. G-70-154

-AA Modification to the Cert ification of the To khe im MaxVac Phase II Vapor Reco very Syste m. G-70-159 -AB Modifiaction of the Certifica tion of the Saber Nozzle fo r Use w it h the Gilb arco VaporV ac Phase ll Vapor Recovery Sys tem. G-70-163

- AA Certificati on of the OPW VaporEZ Phase II Vapo r Recovery System. G-70-164-AA Mo dific ation to the Cert ifi cation of the Has s tech VC P- 3A Vacuum Assist Phase II Vapor Recov ery System. G-70- 165 Healy Vacuum Ass i st Phase II Vapor Recovery System

. G-70-169

- AA Mo dification to the Certification of the Franklin E l ectric INTELLIV AC Phase ll Vapor Recovery System. G-70 -170 Cert ific atio n of the EZ-flo Rebuilt 5005 and 5015 for use with the Balance Phase II Vapor Recov ery Sys tem. G-70-177-AA Certification of the VCS400-7 Vacuum 

### Assist Phas e II Vapor Rec overy Sys tem. G-70 -1 79 Certific ati on of the Catlow IC VN

-V1 Vacuum Assist Phase II Va por Reco very System

. 19

## Stage II Final A m en dme nts Redli ne /St rikeout C opy 12-01-08
G

- 70-180 Order Revoking Certi fication of th e Healy Phase IT Vapor Recovery Systems for Gasoline Dispensing Systems. G-70-183-AA Certification of the Healy/Franklin Vacuum Assist Phase IT Vapor Recovery System. G-70-186 Certification of the Healy Model400 ORVR Vapor Recovery System. G-70-188 Certification of the Catlow ICVN Vapor Recovery Nozzle System for use with the Gilbarco Vap o rVac Vapor Recovery System

. G

- 70-191 H ealy/Franklin V P-1 000 Vapor Pump Phase II Vapor Recovery System(Healy AA ORVR Phase II Vapor Recovery System)_. G-70-196 Certification of the Saber Technologies, LLC SaberVac VR Phase 

## IT Vapor Recovery System G-70-199-AJ Certification of the Gaso l ine Dispens in g Nozzles to the Liquid Retention of 3 50 mil li l eters per 1 ,00 0 Gallons Dis pensed. VR-201-A H ealy System Inc. Phase II E nh anced Vapor Recovery (EVR) System Not Including lSD EVR-202-A H ealy Phase IT Enhanced Vapor Recovery System Including Veeder-Root lSD System G-70-204-A Certification of the Gilbarco Va p o rVac/OPW Vap orsaver ORVR-Com p atible System (j) 

### Department Adopted CARB Stage ll System Executive Orders for Above Ground Storage Tank Vapor Recov ery Systems.

r '**~** 

### Number 

# l Description , 

# r -·-···- - · ··-· ---**·- certific~i-;;** **~~f** 

### a**Ph ~~** **~ Vap~~** **cov ry** **System fu~** **Abovegro~d** 

### Storage 1 

### G

- 70-1 02-A Tanks with less than 40,000 Gall ons Capacity for Gasoline or Gasoline/Met hanol Blended Fuels ' 

### i

.

### -G-70**-116-** F

### rc~**n**Vault

### Above~?und Tank V !il?_? r Recovery System

. . I j 

# !

. G-70- 1 28 ! Bryant Fuel Cell Aboveground Tank Vapor Recove ry System

## --**·G 7o-** **13"0"A ~aui0b~;i!~~~T~**  Vapor

## Recov~ry**_ Sy** **~~em ·-**  - ·----- . - -

- -- -

-- -·--'

### ~-· G-70-131A .I Tank Vault

### Ab~~~~ound T ank

### Va**p~rRecov ery**  System G-70-132-A jsuperva ult Aboveground Tank Vapor Recovery System G

- 70-132-B l sup ervault Abovegro u nd

## Tank_'\'**;f>; R~cov~** **· ~~~**  ..

### ~-·**-- ···** **a::-io-=-i 36**  I FireSafe Abovegro und Tank Vapor R ecovery System : -

### G-70-i**37 ---** **-[F ~e1Safe**  Aboveground Tank Va por Recovery System

-·-----**~----** . -·. . - - .. 

# I

;Phase II Vapor Recovery Systems Installed on Gasoline Bulk j Plants/Di spe nsing Faciliti es with Above ground

### ~anks 

### _ j**---- ---r-~-------~--------~~~~~~** **-- -----------~~**  

### G-70-138 G-70-139 1 1 

### Additi on to the Certification oft h e Hi rt Model VCS-200 Phase II Vapo r Recovery System j integral Phase I and-

- P-

-

h as

_ e

_ I

_ I A

- b

- ov

_

e

_ gr

_o

_

un

_ d

_ T

_

ank

-- C

- o

-'- nfi

- 1

- gur

- ations with fue l Healy Phase II Vapor R ecovery System -"' . 

# r ! 

### G-70-14 0-A \ G-70-142-B ! Phase I Vapor Rec overy Sys tem for Above gro und Gasiline Storage Tanks I ····· ·-····-·- ··-·· ····· ... - · · -- -- · ·-r- --· -· - · -- .. -- . - ·· -'--- • ·:· - ---- .. ------- · --·- -. 

### G

- 70-143 

# WIT Vau lt Abovegr ound Tank Vapor Recovery System



# ------**----------------------~** 20

## Stage II Final Amendments Re dline/S tri keout Copy 12 - 01-08

I 0 _ 70
_147 _A New United Mot ors

### Manuf~ctur~ng, Incorporated Phase II Vapor Recovery

-- System at the Fremont, Cahforma Assembly Plant



## --- " . 

## ·-
. '-·.


## --- 

## -- . 

## --- - ... . . . 

### - - 

### - ... --- 

### - .. 

## --- -
. 

### - . 

# I

.**.9 :?** **0-~~~~ ~~?e** **~~be. ~~<!v** **egr<?~nd** Tank

### Vap~x Rec()very

### Sys~em -- ---- --- - - -·-· 

# I G-70- 1 52
..

# ~e~~!:~,~~~~~::;~ks and Manufacturing Aboveground Tank Vapor**~- ---(}~70-15**  

### 5

. ! Petroleum Marketing**Abo v'~g** **round ank·V** **~p~r 'R~~ov~;ySy~~~-** **-------** 

### .... --- -- . .. . r- o-7o-Is6 .:_ ·

### E~~~it'A~~o~ct**r;~k v** **~~~~ -A:~-;~t** **v~'P~ ;R** **eco ~~cy** **-- sy** **;t~m** - 

# r . G

- 70

- 1S7 J Ecovault

### Ab~v~ground**T;~B~i~ ~~**  ..

### V~p~**R~ ~;,-;cy-** **syst~ --**  .... . . . M 

# f

.... · G= 70 : 1S8-A j Firesafe

## Abo~e~~~~d**T~~k** V apor Recovery System

... . 

# r- · -- - - --- ·- T

-- .. -.. - . .. .. -- . . ------ -·---- -- ------ ..------ - ---·-·-



# . G- :::: :; ..**~::::,::~~!~ ¥~~i:~::P~:~~~~::~** **~~::;_-; ;-Ab-;;~~~;,d**  Ta;,i · -- Vapor Recovery System

·· -- · ·· ...............

## ---- -- ..... 

### - ·--- ' 

### - -

- 

## -- .... ... ......... •.. .. .. ....... . . . 

### [

## 70**16?. _::~** **-J ~!** **~~J.** ..

## :!'**~**

# ..**!.n.~ tit~te** **~~~e~ll:~~A~~~!ound** Tank Vapor Recovery System

--
' 10- 70- 1 67

## ~oVa\llt Aboveground Tank VaP.or Recovery System 

## L

- G-70-168**_I Bry_~t** **~uel sx~t.~~s** **P~ase** 

### I**Vap~~ R~~~~~ry** **·y- ~t~-;** **----- --** **--- ---** **··- ----** 

### ·-~**;0-1 ;~** **----T_ H~ss** **t~~h** 

# VCP

- 3A**Vac~~Assist** Phase

### rrv~p;;**covery** System for

-- ---· I_ 

### ! Aboveground Tank Systems 

# [ o -1o

- 1s1 ··. _

# ~~~~~~~~~~~~~~~l~~~:~**uv~~~~~~sy~~f~ ---·** **~- ·**  Healy Model400 ORVR VaporRecov
. ery System for Aboveground Tank 

# I v1 v1 0 

### Systems 

# I**~~ -;** 

# 90**---""-'-!G uardia** **· C~n** **ai ent,** **Corporation** Armor(:;; ;

### Abovegr~**~~d T;** **~'\rap;r ··**  .. 

# I ! Recovery System

### ----**~~~ ;;;** **--- C~rtifitatio** **-- fth~** **H~;iy M~** **de l4oo** **ORVR N~z~l~** **fo~ Existi~g** 

.

## :Above~~oru:d**Stora~~** Tal1k Systems

- ------- - ----- ---- --- - - -

-- -- - .. -

- ·-- [ Certi fication ofthe Hill-Vac Vapor Recovery System for Cargo T ank Motor G- 70

- 193

__ 

## '!**~h.i.~!e :F.l1~ling**  Systen.:s

### --**·--** ----------. Containment Solutions H oover Vault Aboveground Tank Vapor

### Reco**~ery** 

## l_

## G-70-19~ System ·· - · - . . . .. .... . ... . .**-~** 

### I Cretex**Compani~· -'-** **s, ;::.:** **:.:. ::.~** **=- ..:::.** **c:::.: el** **..;;.: _;** **_; lt** **_; _;** **ro -'-** **un ank**  

### ___ -'-

V

- a

_

p

_ o

_ r

_

R

_ e

_ c...:.

ov

'-

e - ry

__ _ G-70-195 System

### [-**o~7o** 

# i97 -----·**synchrotek F~~3** **Ph~~ iTv~~~it~** **~~ ~cy-s;;;~**  - · - · · 

# r

--=-**G-70 2~~** **-- --** **ldc~tl~ Ab~~~~~~;~d** **B~ lo** **Gr de**  Fuel Vault with

## Bal~;~ V ap;r 

### 1.. ! Recovery System and Buried Vapor Return Piping

r:l

::.:..·

_

### __;.;__~ _ _;;; 

### Oldcastle

### Abo~e~ound**Bel~~ Grade** **F~e l**  Vault w i th

### B~lance Vapor G-70-201 Recovery System and Trenched Vapor Return Piping

### ;:....~------'-'·**--:..., ld** **--'- '-** **-'- st-le** **bov~gro~d Belo~-GradeFuel**  Vault 

### with

### Gilb-~~~0**Vap~rVac** -- G-70

- 202 j 1 

### Phase IT Recovery System and**T~enched** 

### Vapor Return Piping (k) 

### The provisions and requirements of 310 CMR 7.24 (6)(a) and (b) are subject to the 21

## S tage II Final Amendments Redline/S trik e out C opy 12
- 01-08

enforc e ment provi s ions s pecified in 

### 310 C MR 7.52.

22