Dolan Chemical Laboratory

4001 Bixby Road

Groveport, OH 43125

T: 614-836-4221, Audinet 210-4221

F: 614-836-4168, Audinet 210-4168

http://aepenv/labs

Water Analysis

Form REP-703

Rev. 0, 4/2012

Location: Mountaineer Plant Report Date: 11/2/2012

Sample Number: 124373-001 Date Collected: 10/10/2012 09:00 Date Received: 10/10/2012

Plant Outfall #001 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Arsenic, As 2.93 ug/L 0.1 0.03 DPC 10/22/2012 10:31 EPA 200.8

Barium, Ba 94.8 ug/L 0.1 0.03 DPC 10/22/2012 10:31 EPA 200.8

Copper, Cu 4.18 ug/L 0.05 0.02 DPC 10/22/2012 10:31 EPA 200.8

Mercury, Hg 2.8 ng/L 2 0.8 TLT 10/23/2012 EPA 1631E

Nickel, Ni 3.94 ug/L 0.2 0.04 DPC 10/22/2012 10:31 EPA 200.8

Selenium, Se 4.3 ug/L 0.5 0.1 DPC 10/22/2012 10:31 EPA 200.8

Aluminum, Al 0.212 mg/L 0.001 0.0003 DPC 10/22/2012 10:31 EPA 200.8

Iron, Fe 0.158 mg/L 0.01 0.002 DAM 10/18/2012 16:05 EPA 200.7

Chloride, Cl 372 mg/L 2 0.5 TDF 10/30/2012 01:21 EPA 300.1

Sulfate, SO4 1110 mg/L 10 3 TDF 10/30/2012 01:21 EPA 300.1

Sample Number: 124373-002 Date Collected: 10/10/2012 09:00 Date Received: 10/10/2012

Trip Blank 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Mercury, Hg 0.3 ng/L J 0.5 0.2 TLT 10/23/2012 EPA 1631E

Sample Number: 124373-003 Date Collected: 10/10/2012 09:00 Date Received: 10/10/2012

Field Blank 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Mercury, Hg 0.3 ng/L J 0.5 0.2 TLT 10/23/2012 EPA 1631E

Mountaineer Plant, 124373 Page 1 of 5
Location: Mountaineer Plant Report Date: 11/2/2012

Sample Number: 124373-004 Date Collected: 10/09/2012 13:35 Date Received: 10/10/2012

Leachate Underdrain #001 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Arsenic, As 96.0 ug/L 0.1 0.03 DPC 10/22/2012 10:35 EPA 200.8

Barium, Ba 24.1 ug/L 0.1 0.03 DPC 10/22/2012 10:35 EPA 200.8

Cadmium, Cd 6.42 ug/L 0.05 0.01 DPC 10/22/2012 10:35 EPA 200.8

Chromium, Cr 0.8 ug/L 0.2 0.03 DPC 10/22/2012 10:35 EPA 200.8

Lead, Pb 0.188 ug/L 0.01 0.003 DPC 10/22/2012 10:35 EPA 200.8

Mercury, Hg < 0.3 ug/L U 2 0.3 JAB 10/31/2012 EPA 245.2

Molybdenum, Mo 10300 ug/L 0.1 0.02 DPC 10/22/2012 10:35 EPA 200.8

Nickel, Ni 15.7 ug/L 0.2 0.04 DPC 10/22/2012 10:35 EPA 200.8

Selenium, Se 456 ug/L 0.5 0.1 DPC 10/22/2012 10:35 EPA 200.8

Vanadium, V 100 ug/L 2 0.5 DAM 10/18/2012 16:12 EPA 200.7

Zinc, Zn 8.0 ug/L 0.5 0.1 DPC 10/22/2012 10:35 EPA 200.8

Aluminum, Al 0.0835 mg/L 0.001 0.0003 DPC 10/22/2012 10:35 EPA 200.8

Boron, B 75.5 mg/L 0.01 0.002 DAM 10/18/2012 16:12 EPA 200.7

Calcium, Ca 472 mg/L 0.02 0.004 DAM 10/18/2012 16:12 EPA 200.7

Iron, Fe 0.952 mg/L 0.01 0.002 DAM 10/18/2012 16:12 EPA 200.7

Magnesium, Mg 564 mg/L 0.05 0.01 DAM 10/18/2012 16:12 EPA 200.7

Manganese, Mn 2.44 mg/L 0.0005 0.0001 DAM 10/18/2012 16:12 EPA 200.7

Chloride, Cl 933 mg/L 10 2 TDF 10/30/2012 00:21 EPA 300.1

Sulfate, SO4 7240 mg/L 50 20 TDF 10/30/2012 00:21 EPA 300.1

Sample Number: 124373-005 Date Collected: 10/09/2012 13:40 Date Received: 10/10/2012

Leachate Underdrain #007 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Arsenic, As 5.83 ug/L 0.1 0.03 DPC 10/22/2012 10:40 EPA 200.8

Barium, Ba 26.0 ug/L 0.1 0.03 DPC 10/22/2012 10:40 EPA 200.8

Cadmium, Cd 6.69 ug/L 0.05 0.01 DPC 10/22/2012 10:40 EPA 200.8

Chromium, Cr 0.03 ug/L J 0.2 0.03 DPC 10/22/2012 10:40 EPA 200.8

Lead, Pb 0.072 ug/L 0.01 0.003 DPC 10/22/2012 10:40 EPA 200.8

Mercury, Hg < 0.3 ug/L U 2 0.3 JAB 10/31/2012 EPA 245.2

Molybdenum, Mo 10800 ug/L 0.1 0.02 DPC 10/22/2012 10:40 EPA 200.8

Nickel, Ni 24.0 ug/L 0.2 0.04 DPC 10/22/2012 10:40 EPA 200.8

Selenium, Se 261 ug/L 0.5 0.1 DPC 10/22/2012 10:40 EPA 200.8

Vanadium, V < 0.5 ug/L U 2 0.5 DAM 10/18/2012 16:20 EPA 200.7

Zinc, Zn 12.2 ug/L 0.5 0.1 DPC 10/22/2012 10:40 EPA 200.8

Aluminum, Al 0.0167 mg/L 0.001 0.0003 DPC 10/22/2012 10:40 EPA 200.8

Boron, B 29.2 mg/L 0.01 0.002 DAM 10/18/2012 16:20 EPA 200.7

Calcium, Ca 534 mg/L 0.02 0.004 DAM 10/18/2012 16:20 EPA 200.7

Iron, Fe 2.40 mg/L 0.01 0.002 DAM 10/18/2012 16:20 EPA 200.7

Magnesium, Mg 141 mg/L 0.05 0.01 DAM 10/18/2012 16:20 EPA 200.7

Manganese, Mn 3.65 mg/L 0.0005 0.0001 DAM 10/18/2012 16:20 EPA 200.7

Chloride, Cl 61.5 mg/L 2 0.5 TDF 10/30/2012 01:01 EPA 300.1

Sulfate, SO4 2160 mg/L 10 3 TDF 10/30/2012 01:01 EPA 300.1

Mountaineer Plant, 124373 Page 2 of 5
Location: Mountaineer Plant Report Date: 11/2/2012

Sample Number: 124373-006 Date Collected: 10/09/2012 13:45 Date Received: 10/10/2012

Leachate Underdrain #008 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Arsenic, As 177 ug/L 0.1 0.03 DPC 10/22/2012 10:45 EPA 200.8

Barium, Ba 23.8 ug/L 0.1 0.03 DPC 10/22/2012 10:45 EPA 200.8

Cadmium, Cd 6.16 ug/L 0.05 0.01 DPC 10/22/2012 10:45 EPA 200.8

Chromium, Cr 0.8 ug/L 0.2 0.03 DPC 10/22/2012 10:45 EPA 200.8

Lead, Pb 0.272 ug/L 0.01 0.003 DPC 10/22/2012 10:45 EPA 200.8

Mercury, Hg < 0.9 ug/L U 6 0.9 JAB 10/31/2012 EPA 245.2

Molybdenum, Mo 10600 ug/L 0.1 0.02 DPC 10/22/2012 10:45 EPA 200.8

Nickel, Ni 7.57 ug/L 0.2 0.04 DPC 10/22/2012 10:45 EPA 200.8

Selenium, Se 687 ug/L 0.5 0.1 DPC 10/22/2012 10:45 EPA 200.8

Vanadium, V 211 ug/L 2 0.5 DAM 10/18/2012 16:29 EPA 200.7

Zinc, Zn 8.2 ug/L 0.5 0.1 DPC 10/22/2012 10:45 EPA 200.8

Aluminum, Al 0.118 mg/L 0.001 0.0003 DPC 10/22/2012 10:45 EPA 200.8

Boron, B 123 mg/L 0.01 0.002 DAM 10/18/2012 16:29 EPA 200.7

Calcium, Ca 447 mg/L 0.02 0.004 DAM 10/18/2012 16:29 EPA 200.7

Iron, Fe 0.066 mg/L 0.01 0.002 DAM 10/18/2012 16:29 EPA 200.7

Magnesium, Mg 991 mg/L 0.05 0.01 DAM 10/18/2012 16:29 EPA 200.7

Manganese, Mn 1.81 mg/L 0.0005 0.0001 DAM 10/18/2012 16:29 EPA 200.7

Chloride, Cl 1860 mg/L 10 2 TDF 10/30/2012 00:41 EPA 300.1

Sulfate, SO4 12700 mg/L 50 20 TDF 10/30/2012 00:41 EPA 300.1

Sample Number: 124373-007 Date Collected: 10/09/2012 13:50 Date Received: 10/10/2012

Groundwater Interceptor #006 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Arsenic, As 0.92 ug/L 0.1 0.03 DPC 10/22/2012 10:50 EPA 200.8

Barium, Ba 71.9 ug/L 0.1 0.03 DPC 10/22/2012 10:50 EPA 200.8

Cadmium, Cd 0.13 ug/L 0.05 0.01 DPC 10/22/2012 10:50 EPA 200.8

Chromium, Cr 0.4 ug/L 0.2 0.03 DPC 10/22/2012 10:50 EPA 200.8

Lead, Pb 0.063 ug/L 0.01 0.003 DPC 10/22/2012 10:50 EPA 200.8

Mercury, Hg < 0.3 ug/L U 2 0.3 JAB 10/18/2012 EPA 245.2

Molybdenum, Mo 115 ug/L 0.1 0.02 DPC 10/22/2012 10:50 EPA 200.8

Nickel, Ni 1.07 ug/L 0.2 0.04 DPC 10/22/2012 10:50 EPA 200.8

Selenium, Se 5.5 ug/L 0.5 0.1 DPC 10/22/2012 10:50 EPA 200.8

Vanadium, V < 0.5 ug/L U 2 0.5 DAM 10/18/2012 16:37 EPA 200.7

Zinc, Zn 5.9 ug/L 0.5 0.1 DPC 10/22/2012 10:50 EPA 200.8

Aluminum, Al 0.0084 mg/L 0.001 0.0003 DPC 10/22/2012 10:50 EPA 200.8

Boron, B 1.91 mg/L 0.01 0.002 DAM 10/18/2012 16:37 EPA 200.7

Calcium, Ca 260 mg/L 0.02 0.004 DAM 10/18/2012 16:37 EPA 200.7

Iron, Fe 0.020 mg/L 0.01 0.002 DAM 10/18/2012 16:38 EPA 200.7

Magnesium, Mg 93.1 mg/L 0.05 0.01 DAM 10/18/2012 16:37 EPA 200.7

Manganese, Mn 0.0081 mg/L 0.0005 0.0001 DAM 10/18/2012 16:38 EPA 200.7

Chloride, Cl 55.3 mg/L 1 0.2 TDF 10/30/2012 01:48 EPA 300.1

Sulfate, SO4 739 mg/L 5 2 TDF 10/30/2012 01:48 EPA 300.1

Mountaineer Plant, 124373 Page 3 of 5
Location: Mountaineer Plant Report Date: 11/2/2012

Sample Number: 124373-008 Date Collected: 10/09/2012 14:05 Date Received: 10/10/2012

Groundwater Interceptor #007 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Arsenic, As 2.11 ug/L 0.1 0.03 DPC 10/22/2012 10:54 EPA 200.8

Barium, Ba 77.6 ug/L 0.1 0.03 DPC 10/22/2012 10:54 EPA 200.8

Cadmium, Cd 0.09 ug/L 0.05 0.01 DPC 10/22/2012 10:54 EPA 200.8

Chromium, Cr 0.5 ug/L 0.2 0.03 DPC 10/22/2012 10:54 EPA 200.8

Lead, Pb 0.185 ug/L 0.01 0.003 DPC 10/22/2012 10:54 EPA 200.8

Mercury, Hg < 0.3 ug/L U 2 0.3 JAB 10/18/2012 EPA 245.2

Molybdenum, Mo 87.2 ug/L 0.1 0.02 DPC 10/22/2012 10:54 EPA 200.8

Nickel, Ni 1.17 ug/L 0.2 0.04 DPC 10/22/2012 10:54 EPA 200.8

Selenium, Se 4.5 ug/L 0.5 0.1 DPC 10/22/2012 10:54 EPA 200.8

Vanadium, V < 0.5 ug/L U 2 0.5 DAM 10/18/2012 16:41 EPA 200.7

Zinc, Zn 4.1 ug/L 0.5 0.1 DPC 10/22/2012 10:54 EPA 200.8

Aluminum, Al 0.0616 mg/L 0.001 0.0003 DPC 10/22/2012 10:54 EPA 200.8

Boron, B 1.34 mg/L 0.01 0.002 DAM 10/18/2012 16:41 EPA 200.7

Calcium, Ca 212 mg/L 0.02 0.004 DAM 10/18/2012 16:41 EPA 200.7

Iron, Fe 0.081 mg/L 0.01 0.002 DAM 10/18/2012 16:41 EPA 200.7

Magnesium, Mg 68.7 mg/L 0.05 0.01 DAM 10/18/2012 16:41 EPA 200.7

Manganese, Mn 0.0579 mg/L 0.0005 0.0001 DAM 10/18/2012 16:41 EPA 200.7

Chloride, Cl 43.0 mg/L 1 0.2 TDF 10/30/2012 02:08 EPA 300.1

Sulfate, SO4 592 mg/L 5 2 TDF 10/30/2012 02:08 EPA 300.1

Sample Number: 124373-009 Date Collected: 10/09/2012 14:10 Date Received: 10/10/2012

Groundwater Interceptor Sump 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Arsenic, As 4.36 ug/L 0.1 0.03 DPC 10/22/2012 11:57 EPA 200.8

Barium, Ba 53.5 ug/L 0.1 0.03 DPC 10/22/2012 11:57 EPA 200.8

Cadmium, Cd 1.14 ug/L 0.05 0.01 DPC 10/22/2012 11:57 EPA 200.8

Chromium, Cr 3.3 ug/L 0.2 0.03 DPC 10/22/2012 11:57 EPA 200.8

Lead, Pb 0.392 ug/L 0.01 0.003 DPC 10/22/2012 11:57 EPA 200.8

Mercury, Hg < 0.3 ug/L U 2 0.3 JAB 10/18/2012 EPA 245.2

Molybdenum, Mo 1100 ug/L 0.1 0.02 DPC 10/22/2012 11:57 EPA 200.8

Nickel, Ni 7.92 ug/L 0.2 0.04 DPC 10/22/2012 11:57 EPA 200.8

Selenium, Se 40.5 ug/L 0.5 0.1 DPC 10/22/2012 11:57 EPA 200.8

Vanadium, V < 0.5 ug/L U 2 0.5 DAM 10/18/2012 16:45 EPA 200.7

Zinc, Zn 9.2 ug/L 0.5 0.1 DPC 10/22/2012 11:57 EPA 200.8

Aluminum, Al 0.0242 mg/L 0.001 0.0003 DPC 10/22/2012 11:57 EPA 200.8

Boron, B 9.98 mg/L 0.01 0.002 DAM 10/18/2012 16:45 EPA 200.7

Calcium, Ca 263 mg/L 0.02 0.004 DAM 10/18/2012 16:45 EPA 200.7

Iron, Fe 0.076 mg/L 0.01 0.002 DAM 10/18/2012 16:45 EPA 200.7

Magnesium, Mg 109 mg/L 0.05 0.01 DAM 10/18/2012 16:45 EPA 200.7

Manganese, Mn 0.763 mg/L 0.0005 0.0001 DAM 10/18/2012 16:45 EPA 200.7

Chloride, Cl 131 mg/L 1 0.2 TDF 10/30/2012 02:27 EPA 300.1

Sulfate, SO4 1260 mg/L 5 2 TDF 10/30/2012 02:27 EPA 300.1

Mountaineer Plant, 124373 Page 4 of 5
Location: Mountaineer Plant Report Date: 11/2/2012

Sample Number: 124373-010 Date Collected: 10/08/2012 14:23 Date Received: 10/10/2012

CPS Effluent 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Mercury, Hg 36.1 ng/L 10 4 TLT 10/23/2012 EPA 1631E

Sample Number: 124373-011 Date Collected: 10/10/2012 08:20 Date Received: 10/10/2012

CPS Effluent 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Mercury, Hg 31.0 ng/L 10 4 TLT 10/23/2012 EPA 1631E

Sample Number: 124373-012 Date Collected: 10/10/2012 08:25 Date Received: 10/10/2012

Bioreactor Effluent 

Parameter Result Units RL MDL Analysis By Analysis Date/Time Method

Data 

Qual

Mercury, Hg 1.8 ng/L 1 0.4 TLT 10/23/2012 EPA 1631E

THIS TEST REPORT RELATES ONLY TO THE ITEMS TESTED AND SHALL NOT BE REPRODUCED EXCEPT IN FULL WITHOUT WRITTEN 

APPROVAL OF THE LABORATORY. ALL TEST RESULTS MEET ALL OF THE REQUIREMENTS OF THE ACCREDITING AUTHORITY, 

UNLESS OTHERWISE NOTED.

U: Analyte was analyzed and not detected at or above adjusted Method Detection Limit

J: Analyte was positively identified, though the quantitation was below Reporting Limit.

Brian Snyder, Chemist II

Email bssnyder@aep.com Tel. 614-836-4224

Fax 614-836-4168 Audinet 210-4224

Mountaineer Plant, 124373 Page 5 of 5