Notes from Site Visit at Duke Energy’s Gibson Generating Station on February 24, 2009 (Public Version)Page 2

Notes from Site Visit at Duke Energy’s Gibson Generating Station on February 24, 2009 (Public Version)

EPA conducted a site visit at Duke Energy’s Gibson Generating Station (Gibson) located in Gibson County, IN on Tuesday, February 24, 2009 to learn about the operations at the plant

, specifically the deepwell injection of FGD wastewater and planned conversions to dry fly ash handling

. Table 2, located at the end of these notes , identifies the site visit participants. The presentation that the Gibson personnel gave during the site visit is provided as Attachment 1 to
th ese notes

.

These notes describe the information collected during th e site visit and the pre

- site visit phone call, which was held on February 1 3 , 2009.

Plant Overview

**•** Gibson operates five coal

- fired generating units at the plant

. The table below contains some general information on the current operation of each steam e lectric generating unit.

Table 1. Gibson Generating Station Unit Operations

Unit Installation
Date Gross Capacity (MW) Particulate Control NOx Control SO 2 Control

1 5/3/1976 670 ESP (cold

- side) Selective catalytic reduction (SCR) Wet flue gas
desulfuri zation (FGD)

2 4/16/1975 670 ESP (cold

- side) SCR Wet FGD
3 3/28/1978 670 ESP (cold

- side) SCR Wet FGD

4 3/27/1979 670 ESP (cold

- side) SCR Wet FGD
5 10/1/1982 670 ESP (cold

- side) SCR Wet FGD

**•** Gibson burns about 29,000 tons of coal per day. The majority of their coal is Illinois Basin coal, with sulfur concentrations ranging from 1.5 to 5 lbs
SO 2 /MMBTU, but more typically 4.5 to 5.0 SO 2 /MMBTU . The chlorine content of the coal ranges from 0.2 to 0.25% by weight.

**•** [ Redacted out Confidential Business Informa tion.]

**•** Gibson is a zero discharge plant and, therefore, does not have a NPDES permit. The Gibson plant transfers certain process water to its unlined manmade cooling pond, which covers 3,000 acres and is generally 10 to 12 feet deep. The cooling pond also provides the service water for the plant. As needed, the plant pulls water from the Wabash River into the cooling pond, but the cooling pond does not discharge to the Wabash River. [ Redacted out Confidential Business Information.]Page 3

FGD Systems

**•** Gibson sta ted that they use service water (i.e., cooling pond water) for limestone slurry make up, mist eliminator wash water, gypsum washing (Units 1, 2, and 3 only), and make

- up water to the FGD.

**•** Gibson stated that they can use a blend of service water and reclai m water for gypsum washing, limestone slurry make

- up, and make

- up to the FGD, but they try to use as much service water as possible for the mist eliminator wash. [ Redacted out Confidential Business Information.]

Units 1, 2, and 3 FGD Systems

**•** The Units 1, 2, and 3 FGD systems are all single tower, limestone forced oxidation scrubbers. The FGDs were installed at the following times:

**•** Unit 1

– Fall 2007;

**•** Unit 2

– Spring 2007; and

**•** Unit 3

– Winter 2006.

**•** [ Redacted out Confidential Business Information.]

**•** [ Redac ted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redact ed out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

Unit 4 FGD System

**•** The Unit 4 FGD system is a dual tower, limestone inhibited oxidation FGD
scrubber. Gibson a dds emulsified sulfur to the scrubber to prevent the oxidation of calcium sulfite to gypsum.

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]Page 4

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

Unit 5 FGD System

**•** The Unit 5 FGD system is a horizontal flow, limestone forced oxidation FGD system. Gibson stated that the FGD was originally designed for inhibi ted oxidation, but it was recently converted to increase sulfur dioxide removals. The #5 FGD was converted to forced oxidation in spring June 2008. [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Red acted out Confidential Business Information.]

**•** Gibson stated that fixating gypsum is the same as fixating calcium sulfite.

**•** [ Redacted out Confidential Business Information.]

FGD Solids Disposal

**•** Gibson stated that Units 1, 2, and 3 have a shared gypsum s tacker, but Units 4 and
5 each have their own FGD solids stacker. Gibson collects the solids from the stacker pads and trucks it to the on

- site landfill. The gypsum solids from Units 1, 2, and 3 and the pozzolanic materials from Units 4 and 5 are commingle d within
the landfill.

FGD W astewater Treatment and Disposal

FGD Wastewater Treatment

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]Page 5

FGD Wastewater Disposal

**•** [ Redacted out Confidential Business Information.]

**•** Gibson currently has three nonhazardous injection wells on site. The wells are approximately 12,000 feet deep and cased to 5,200 feet. The ground level footprint is 150’ x 150’. The surface casin g goes to 500 feet.

**•** Well 1 currently has a test injection permit. Gibson began injecting some amount of wastewater down Well 1 in June/July 2007, [ Redacted out Confidential Business Information.]

**•** Gibson stated that Wells 2 and 3 are almost complete.

**•** [ Re dacted out Confidential Business Information.]

**•** Gibson stated that their contractors have been monitoring TSS, pH, chlorides, calcium, magnesium, and sulfate to determine whether the wastewater is safe to be deep well injected.

Ash Handling

**•** Gibson is co nvert ing Units 1

- 3 to dry fly ash handling. They currently expect conversion to begin in Fall 2011 and to be complete by Spring 2012. Construction on all units is expected to be simultaneous with scheduled outages. [ Redacted out Confidential Business Inf ormation.]

**•** Gibson does not expect much change in equipment for the conversion. Currently the vacuum pulls ash out of the hoppers, mixes with water, and transfers to the pond. For dry handling, they will still use the trunk line, but will add piping from

t he trunk to the filter separation tank. The ash in the separator tank from Unit 3 will be blown to Units 1 and 2 transfer bins. Ash from Units 1 and 2 will drop directly into the transfer bins.

**•** All bottom ash handling is wet. [ Redacted out Confidential Bu siness Information.]

Ash Ponds

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** [ Redacted out Confidential Business Information.]

**•** Gibson’s ash pond pr eviously used in the 1980s was closed in 2005.Page 6

**•** Following conversion to dry fly ash handling, Gibson plans to transfer bottom ash sluice water only to the North Ash Pond.

On

- Site Landfills

**•** Gibson operates two on

- site landfills: South Landfill and the Fix ated Scrubber Sludge (FSS) Landfill.

**•** Gibson ’s South Landfill includes 377 permitted acres. Thirteen acres are currently open. The landfill leachate collects in a separate pond which discharges directly to the cooling pond.

**•** The FSS Landfill, named in 198 2, accepts all solids generated at the plant. Fixated materials generated from Units 4 and 5 are stored alongside ash and other solids. Gibson does not segregate the wastes in the landfill. Leachate from this landfill flows into North Basin, and ultimately to the cooling pond.Page 4

Table 2 . Site Visit Attendees

Name Organization (Representing) Telephone E

- mail

Becky Sparks Gibson Station

– Environmental
Coordinator 812

- 386

- 4202 rebecca.sparks@duke

- energy.com

Mick Harpenau Gibson

– Engineering 812

- 386

- 4886 mick.harpenau@duke

- energy.com

Tom McClellan Gibson

– Engineering

- Retired Retired Retired

Debbie Nispel Duke Energy 317

- 838

- 1957 debbie.nispel@duke

- energy.com

Robert Wylie Duke Energy 704

- 382

- 4669 rrwylie@duke

- energy.com

Mike Judd Duke Energy 317

- 838

- 1729 mike.judd@duke

- energy.com

Howard Lewis Duke Energy

- Retired Retired Retired

Jim Meiers Duke Energy 317

- 838

- 1955 jim.meiers@duke

- energy.com

Rick Cleveland Duke Energy 812

- 386

- 4146 rick.cleveland@duke

- energy.com

Donna Hill UWAG 205

- 257

- 5234 dbhill@southernco.com

Keith Condra Indiana DEM 812

- 380

- 2311 kcondra@idem.in.gov

Ron Jordan EPA/Office of Water 202

- 566

- 1003 jordan.ronald@epa.gov

Deb Bartram ERG (Contractor to EPA) 703

- 633

- 1669 deborah.bartram@erg.com

174918 5

. 2