Name: John M. MacDonald

Title: Vice President - Generation

Company: Public Service Company of New Ham

Sign Date: 9/3/2010

Name: David A. Caron

Title: VP of Monitoring Services

Company: Eastmount Environmetntal Services

Sign Date: 9/3/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 01, 2011 Page 1 of 10
9/3/2010

Facility Information:

NH Merrimack

97 River Rd.

Bow NH 03304

Contact: Roger Deshaies

Phone: (603) 228- 2081 Ext 4173

Fax:

Email:

Testing Company:

Eastmount Environmental Services, LLC

65 Parker Street, Suite 3

Newburyport MA 01950

Contact:Mr. David A. Caron

Phone: (978) 499-9300 x11

Fax: (978) 499-9303

Email: dcaron@eastmount.com

Air Permit Number: Permitted Source ID/Name:

2364 3301300026

Permitted Maximum Process Rate: Max. Normal Operation Process Rate: Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description 10100203 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Cyclone Furnace (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Outlet 194 0 0 9.2 5.4 9.2 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Organic Condensible 

Particulate

Stack Outlet OTM - 27/28 3 360 0

Stack Outlet Total PM2.5 OTM - 27/28 3 360 0

Inorganic (Aqueous) 

Condensible Part.

Stack Outlet OTM - 27/28 3 360 0

Stack Outlet Filterable Particulate Method 29 3 240 0

Stack Outlet Antimony Method 29 3 240 0

Stack Outlet Arsenic Method 29 3 240 0

Tuesday, February 01, 2011 Page 2 of 10
9/3/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Stack Outlet Manganese Method 29 3 240 0

Stack Outlet Beryllium Method 29 3 240 0

Stack Outlet Cobalt Method 29 3 240 0

Stack Outlet Cadmium Method 29 3 240 0

Stack Outlet Lead Method 29 3 240 0

Stack Outlet Selenium Method 29 3 240 0

Stack Outlet Nickel Method 29 3 240 0

Stack Outlet Chromium Method 29 3 240 0

Stack Outlet O2 Method 3A O2 3 240 0

Stack Outlet Co2 Method 3A CO2 3 240 0

Tuesday, February 01, 2011 Page 3 of 10
9/3/2010

Sampling / Stack Data Results Summary

Location Stack Outlet - Method 29

Average

Run Number M5-1 M5-2 M5-3

Test Date 3/29/2010 3/30/2010 3/31/2010

Run Start Time 11:35:00 AM 7:35:00 

AM

7:40:00 AM

Run Finish Time 4:16:00 PM 12:03:00 

PM

12:04:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 141.906 141.676 145.771 143.118

Moisture Content of Stack Gas, % 7.66 8.29 8.34 8.097

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 15.54 15.43 15.31 15.427

Oxygen, % 3.76 3.83 3.88 3.823

Average Stack Gas Temperature, °F 335.56 335.54 334.94 335.347

Dry Volumetric Flow Rate, dry scfm 626,241.9 628,862.6 629,782.0 628,295.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,044,552.2 1,055,021.1 1,060,686.6 1,053,419.96

7

Percent Isokinetic of Sampling Rate, % 100.5 100.0 102.7 101.067

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Tuesday, February 01, 2011 Page 4 of 10
9/3/2010

Location Stack Outlet - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Tuesday, February 01, 2011 Page 5 of 10
9/3/2010

Emissions Summary

Location: Stack Outlet - Method 29

Compound: Antimony

Average

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.0159 0.0156 0.0159 0.016

lb/mmBtuCO2 2.89E-06 2.77E-06 2.86E-06 0.000

Compound: Arsenic

Average

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.0878 0.0838 0.092 0.088

lb/mmBtuCO2 1.59E-05 1.49E-05 1.66E-05 0.000

Compound: Beryllium

Average

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.00562 0.00564 0.00574 0.006

lb/mmBtuCO2 1.02E-06 1.00E-06 1.03E-06 0.000

Compound: Cadmium

Average

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.00357 0.00839 0.00366 0.005

lb/mmBtuCO2 6.48E-07 1.49E-06 6.59E-07 0.000

Compound: Chromium

Average

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.0983 0.0938 0.1019 0.098

lb/mmBtuCO2 1.78E-05 1.67E-05 1.83E-05 0.000

Compound: Cobalt

Average

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.01036 0.0099 0.00961 0.010

lb/mmBtuCO2 1.88E-06 1.76E-06 1.73E-06 0.000

Compound: Filterable Particulate

Average

RunNumber M5-3 M5-1 M5-2

Mass_mg 127.5 138.2 273 179.567

lb/mmBtuCO2 2.27E-02 2.49E-02 4.96E-02 0.032

Compound: Lead

Average

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.0438 0.0417 0.0411 0.042

lb/mmBtuCO2 7.95E-06 7.41E-06 7.40E-06 0.000

Compound: Manganese

Average

Tuesday, February 01, 2011 Page 6 of 10
9/3/2010

Process Run Data

RunNumber M5-2 M5-3 M5-1

Mass_mg 0.0514 0.0491 0.0484 0.050

lb/mmBtuCO2 9.33E-06 8.73E-06 8.71E-06 0.000

Compound: Nickel

Average

RunNumber M5-3 M5-1 M5-2

Mass_mg 0.0467 0.0516 0.0494 0.049

lb/mmBtuCO2 8.30E-06 9.29E-06 8.97E-06 0.000

Compound: Selenium

Average

RunNumber M5-3 M5-1 M5-2

Mass_mg 0.6037 0.4456 0.45 0.500

lb/mmBtuCO2 1.07E-04 8.02E-05 8.17E-05 0.000

Location: Stack Outlet - OTM - 27/28

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber OTM27/28 - R1 OTM27/28 - R2 OTM27/28 - R3

Mass_mg 4.2 240 320 188.067

lb/mmBtuCO2 8.55E-04 4.81E-02 6.82E-02 0.039

Compound: Organic Condensible Particulate

Average

RunNumber OTM27/28 - R1 OTM27/28 - R2 OTM27/28 - R3

Mass_mg 240 13 4.1 85.700

lb/mmBtuCO2 4.89E-02 2.61E-03 8.74E-04 0.017

Compound: Total PM2.5

Average

RunNumber OTM27/28 - R1 OTM27/28 - R2 OTM27/28 - R3

Mass_mg 56.6 48.5 47.5 50.867

lb/mmBtuCO2 1.15E-02 9.73E-03 1.01E-02 0.010

Tuesday, February 01, 2011 Page 7 of 10
9/3/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Bituminous Coal Burned 0 1000 Tons 0

Run Name Value UOM Comments

Target

Value

1 SCR (SELECTIVE CATALYTIC REDUCTION) 0 0

1 ELECTROSTATIC PRECIPITATOR 0 0

Tuesday, February 01, 2011 Page 8 of 10
9/3/2010

Sampling / Stack Data Results Detail

Location Stack Outlet - Method 29

Average

Run Number M5-1 M5-2 M5-3

Test Date 3/29/2010 3/30/2010 3/31/2010

Run Start Time 11:35:00 AM 7:35:00 AM 7:40:00 AM

Run Finish Time 4:16:00 PM 12:03:00 PM 12:04:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.188 0.188 0.188 0.188

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.0059 1.0059 1.0059 1.006

Barometric Pressure, inches of Mercury 29.34 29.37 29.25 29.320

Average Orifice Meter Differential, inches H2O 1.22 1.24 1.25 1.237

Dry Gas Meter Volume Sampled, cubic feet 142.560 137.899 144.094 141.518

Average Dry Gas Meter Temperature, °F 64.82 49.03 54.86 56.237

Dry Gas Meter Volume Sampled, dscf 141.906 141.676 145.771 143.118

Total Moisture Liquid collected, g 250 272 282 268.000

Volume of Water Vapor, standard cubic feet 11.77 12.80 13.27 12.613

Moisture Content of Stack Gas, % 7.66 8.29 8.34 8.097

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9234 0.9171 0.9166 0.919

Carbon Dioxide, % 15.54 15.43 15.31 15.427

Oxygen, % 3.76 3.83 3.88 3.823

Carbon Monoxide & Nitrogen, % 80.7 80.74 80.81 80.750

Fuel Factor 1.10 1.11 1.11

Dry Molecular Weight, lb/lb-Mole 30.64 30.62 30.60 30.620

Wet Molecular weight, lb/lb-Mole 29.67 29.57 29.55 29.597

Flue Gas Static Pressure, inches of H2O -0.9 -0.89 -0.9 -0.897

Absolute Flue Gas Pressure, inches of Mercury 29.27 29.30 29.18 29.250

Average Stack Gas Temperature, °F 335.56 335.54 334.94 335.347

Average Velocity Head, inches of H2O 1.5224214902

248

1.549455309

58402

1.559895561

02448

1.544

Average Stack Gas Velocity, feet/second 84.81 85.66 86.12 85.530

Stack Cross-Sectional Area, square feet 205.273 205.273 205.273 205.273

Dry Volumetric Flow Rate, dry scfm 626,241.9 628,862.6 629,782.0 628,295.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,044,552.2 1,055,021.1 1,060,686.6 1,053,419.9

67

Percent Isokinetic of Sampling Rate, % 100.5 100.0 102.7 101.067

Percent Excess Air, % 21.4 21.9 22.2 21.833

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 194 194 194

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Tuesday, February 01, 2011 Page 9 of 10
9/3/2010

Location Stack Outlet - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Tuesday, February 01, 2011 Page 10 of 10