Name: Dan Giovanni

Title: Manager, Power Supply Operations an

Company: Hawaiian Electric Company, Inc.

Sign Date: 7/2/2010

Name: Tony Wong

Title: President

Company: AirKinetics Inc.

Sign Date: 7/2/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Emissions Testing Unit 7

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 10, 2011 Page 1 of 25
Emissions Testing Unit 7

7/2/2010

Facility Information:

HI, Waiau

475 Kamehameha Highway

Pearl City HI 96782

Contact: Stephen Ward

Phone: (808) 543-4535

Fax: (808) 543-4511

Email: stephen.ward@heco.com

Testing Company:

AirKinetics Inc.

1308 S. Allec

Anaheim CA 92805

Contact:Tony Wong

Phone: (714) 245-1945

Fax: (714) 956-2350

Email: wongt@airkineticsinc.com

Air Permit Number:

0239-01-C

Permitted Source ID/Name:

7

Permitted Maximum Process Rate:

923 MMBtu/hr

Max. Normal Operation Process Rate:

863 MMBtu/hr

Target Process Test Rate

842 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1500300502 FRS #: 110000486420

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Tangential Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack 122 0 0 122 327 336 2 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack Carbon Monoxide Method 10 3 120 0

stack 2,3,7,8-TCDD Method 23 3 480 0

stack 1,2,3,7,8-PeCDD Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Regulation Description Compound Limit Unit

Thursday, February 10, 2011 Page 2 of 25
Emissions Testing Unit 7

7/2/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

stack OCDD Method 23 3 480 0

stack 2,3,7,8-TCDF Method 23 3 480 0

stack 1,2,3,7,8-PeCDF Method 23 3 480 0

stack 2,3,4,7,8-PeCDF Method 23 3 480 0

stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

stack OCDF Method 23 3 480 0

stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

stack Method 23 3 480 0

stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

stack Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

stack Method 25A 3 120 0

stack Hydrogen Fluoride Method 26 3 60 0

stack Hydrogen Chloride Method 26 3 60 0

stack Total PM2.5 OTM - 27/28 3 367 0

stack Beryllium Method 29 3 240 0

stack Arsenic Method 29 3 240 0

stack Cadmium Method 29 3 240 0

stack Chromium Method 29 3 240 0

stack Cobalt Method 29 3 240 0

stack Lead Method 29 3 240 0

stack Manganese Method 29 3 240 0

stack Nickel Method 29 3 240 0

stack Selenium Method 29 3 240 0

stack Antimony Method 29 3 240 0

stack O2 Method 3A O2 3 120 0

stack Co2 Method 3A CO2 3 120 0

stack Filterable Particulate Method 5 3 240 0

stack Sulfur Dioxide Method 6C 3 120 0

stack Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, February 10, 2011 Page 3 of 25
Emissions Testing Unit 7

7/2/2010

Thursday, February 10, 2011 Page 4 of 25
Emissions Testing Unit 7

7/2/2010

Sampling / Stack Data Results Summary

Location stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 23

Average

Run Number 1 2 3

Test Date 4/2/2010 4/5/2010 4/7/2010

Run Start Time 7:48:00 AM 7:40:00 

AM

7:41:00 AM

Run Finish Time 4:13:00 PM 4:07:00 PM 4:08:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 401.741 393.834 401.162 398.912

Moisture Content of Stack Gas, % 10.92 10.97 11.18 11.023

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.6 11.9 12.4 11.967

Oxygen, % 5.4 4.8 4.9 5.033

Average Stack Gas Temperature, °F 311.79 306.21 306.46 308.153

Dry Volumetric Flow Rate, dry scfm 186,240.9 182,858.6 183,471.9 184,190.467

Actual Wet Volumetric Flue Gas Flow Rate, acfm 304,181.5 297,654.6 299,456.8 300,430.967

Percent Isokinetic of Sampling Rate, % 99.7 99.6 101.1 100.133

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 5 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 6 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 7 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 10, 2011 Page 8 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 10, 2011 Page 9 of 25
Emissions Testing Unit 7

7/2/2010

Emissions Summary

Location: stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 4.21E-04 6.59E-04 1.31E-03 0.001

ppm 5.03E-01 7.90E-01 1.57E+00 0.954

ppm@7%O2 4.19E-01 6.56E-01 1.30E+00 0.792

Location: stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000127 0.0000000195 0.0000000167 0.000

lb/mmBtuO2 8.64E-13 1.30E-12 1.10E-12 0.000

ng/dscm 1.12E-03 1.75E-03 1.47E-03 0.001

ng/dscm@7%O2 1.00E-03 1.51E-03 1.28E-03 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000151 0.0000000111 0.00000000687 0.000

lb/mmBtuO2 1.03E-12 7.41E-13 4.53E-13 0.000

ng/dscm 1.33E-03 9.95E-04 6.05E-04 0.001

ng/dscm@7%O2 1.19E-03 8.59E-04 5.26E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000933 0.0000000092 0.0000000178 0.000

lb/mmBtuO2 6.34E-13 6.14E-13 1.17E-12 0.000

ng/dscm 8.20E-04 8.25E-04 1.57E-03 0.001

ng/dscm@7%O2 7.35E-04 7.12E-04 1.36E-03 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000124 0.0000000122 0.000000014 0.000

lb/mmBtuO2 8.43E-13 8.15E-13 9.24E-13 0.000

ng/dscm 1.09E-03 1.09E-03 1.23E-03 0.001

ng/dscm@7%O2 9.77E-04 9.41E-04 1.07E-03 0.001

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000559 0.0000000069 0.00000000496 0.000

lb/mmBtuO2 3.80E-13 4.61E-13 3.27E-13 0.000

ng/dscm 4.91E-04 6.19E-04 4.37E-04 0.001

ng/dscm@7%O2 4.40E-04 5.34E-04 3.80E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

Thursday, February 10, 2011 Page 10 of 25
Emissions Testing Unit 7

7/2/2010

RunNumber 1 2 3

Mass_mg 0.0000000115 0.0000000113 0.0000000197 0.000

lb/mmBtuO2 7.82E-13 7.55E-13 1.30E-12 0.000

ng/dscm 1.01E-03 1.01E-03 1.73E-03 0.001

ng/dscm@7%O2 9.06E-04 8.72E-04 1.50E-03 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000102 0.00000000464 0.00000000466 0.000

lb/mmBtuO2 6.94E-13 3.10E-13 3.07E-13 0.000

ng/dscm 8.97E-04 4.16E-04 4.10E-04 0.001

ng/dscm@7%O2 8.04E-04 3.59E-04 3.56E-04 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000112 0.000000011 0.0000000192 0.000

lb/mmBtuO2 7.62E-13 7.35E-13 1.27E-12 0.000

ng/dscm 9.85E-04 9.87E-04 1.69E-03 0.001

ng/dscm@7%O2 8.83E-04 8.52E-04 1.47E-03 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000447 0.00000000591 0.00000000594 0.000

lb/mmBtuO2 3.04E-13 3.95E-13 3.92E-13 0.000

ng/dscm 3.93E-04 5.30E-04 5.23E-04 0.000

ng/dscm@7%O2 3.52E-04 4.58E-04 4.54E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000993 0.00000000657 0.00000000698 0.000

lb/mmBtuO2 6.75E-13 4.39E-13 4.60E-13 0.000

ng/dscm 8.73E-04 5.89E-04 6.15E-04 0.001

ng/dscm@7%O2 7.83E-04 5.09E-04 5.34E-04 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000112 0.00000000791 0.0000000106 0.000

lb/mmBtuO2 7.62E-13 5.28E-13 6.99E-13 0.000

ng/dscm 9.85E-04 7.09E-04 9.33E-04 0.001

ng/dscm@7%O2 8.83E-04 6.12E-04 8.11E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.000000014 0.0000000111 0.0000000172 0.000

lb/mmBtuO2 9.52E-13 7.41E-13 1.13E-12 0.000

ng/dscm 1.23E-03 9.95E-04 1.51E-03 0.001

ng/dscm@7%O2 1.10E-03 8.59E-04 1.31E-03 0.001

Thursday, February 10, 2011 Page 11 of 25
Emissions Testing Unit 7

7/2/2010

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000126 0.0000001584 0.0000001662 0.000

lb/mmBtuO2 8.57E-12 1.06E-11 1.10E-11 0.000

ng/dscm 1.11E-02 1.42E-02 1.46E-02 0.013

ng/dscm@7%O2 9.95E-03 1.23E-02 1.27E-02 0.012

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000509 0.000000866 0.00000119 0.000

lb/mmBtuO2 3.46E-11 5.78E-11 7.85E-11 0.000

ng/dscm 4.47E-02 7.77E-02 1.05E-01 0.076

ng/dscm@7%O2 4.01E-02 6.71E-02 9.12E-02 0.066

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000429 0.0000000636 0.0000000699 0.000

lb/mmBtuO2 2.92E-12 4.25E-12 4.61E-12 0.000

ng/dscm 3.77E-03 5.70E-03 6.15E-03 0.005

ng/dscm@7%O2 3.38E-03 4.92E-03 5.34E-03 0.005

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000464 0.0000000545 0.000000074 0.000

lb/mmBtuO2 3.16E-12 3.64E-12 4.88E-12 0.000

ng/dscm 4.08E-03 4.89E-03 6.52E-03 0.005

ng/dscm@7%O2 3.66E-03 4.22E-03 5.66E-03 0.005

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000125 0.0000025 0.00000337 0.000

lb/mmBtuO2 8.50E-11 1.67E-10 2.22E-10 0.000

ng/dscm 1.10E-01 2.24E-01 2.97E-01 0.210

ng/dscm@7%O2 9.86E-02 1.93E-01 2.58E-01 0.183

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000047 0.0000000613 0.0000000766 0.000

lb/mmBtuO2 3.20E-12 4.09E-12 5.05E-12 0.000

ng/dscm 4.13E-03 5.50E-03 6.74E-03 0.005

ng/dscm@7%O2 3.70E-03 4.75E-03 5.86E-03 0.005

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000038 0.00000000502 0.00000000505 0.000

lb/mmBtuO2 2.58E-13 3.35E-13 3.33E-13 0.000

Thursday, February 10, 2011 Page 12 of 25
Emissions Testing Unit 7

7/2/2010

ng/dscm 3.34E-04 4.50E-04 4.45E-04 0.000

ng/dscm@7%O2 3.00E-04 3.89E-04 3.87E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000116 0.0000000153 0.000000011 0.000

lb/mmBtuO2 7.89E-13 1.02E-12 7.26E-13 0.000

ng/dscm 1.02E-03 1.37E-03 9.68E-04 0.001

ng/dscm@7%O2 9.15E-04 1.18E-03 8.41E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000852 0.0000000116 0.0000000133 0.000

lb/mmBtuO2 5.79E-13 7.75E-13 8.77E-13 0.000

ng/dscm 7.49E-04 1.04E-03 1.17E-03 0.001

ng/dscm@7%O2 6.72E-04 8.98E-04 1.02E-03 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000898 0.0000000142 0.0000000149 0.000

lb/mmBtuO2 6.11E-13 9.48E-13 9.83E-13 0.000

ng/dscm 7.89E-04 1.27E-03 1.31E-03 0.001

ng/dscm@7%O2 7.08E-04 1.10E-03 1.14E-03 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000411 0.0000000625 0.000000033 0.000

lb/mmBtuO2 2.79E-12 4.17E-12 2.18E-12 0.000

ng/dscm 3.61E-03 5.61E-03 2.91E-03 0.004

ng/dscm@7%O2 3.24E-03 4.84E-03 2.53E-03 0.004

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000499 0.0000000615 0.0000000868 0.000

lb/mmBtuO2 3.39E-12 4.11E-12 5.73E-12 0.000

ng/dscm 4.39E-03 5.52E-03 7.64E-03 0.006

ng/dscm@7%O2 3.94E-03 4.77E-03 6.64E-03 0.005

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000242 0.000000328 0.000000376 0.000

lb/mmBtuO2 1.65E-11 2.19E-11 2.48E-11 0.000

ng/dscm 2.13E-02 2.94E-02 3.31E-02 0.028

ng/dscm@7%O2 1.91E-02 2.54E-02 2.88E-02 0.024

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Thursday, February 10, 2011 Page 13 of 25
Emissions Testing Unit 7

7/2/2010

Mass_mg 0.0000000301 0.0000000683 0.000000163 0.000

lb/mmBtuO2 2.05E-12 4.56E-12 1.08E-11 0.000

ng/dscm 2.65E-03 6.13E-03 1.44E-02 0.008

ng/dscm@7%O2 2.38E-03 5.29E-03 1.25E-02 0.007

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000308 0.0000000534 0.0000000244 0.000

lb/mmBtuO2 2.09E-12 3.57E-12 1.61E-12 0.000

ng/dscm 2.71E-03 4.79E-03 2.15E-03 0.003

ng/dscm@7%O2 2.43E-03 4.14E-03 1.87E-03 0.003

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000173 0.000000017 0.0000000187 0.000

lb/mmBtuO2 1.18E-12 1.14E-12 1.23E-12 0.000

ng/dscm 1.52E-03 1.52E-03 1.65E-03 0.002

ng/dscm@7%O2 1.36E-03 1.31E-03 1.43E-03 0.001

Location: stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 1.24E-03 6.45E-04 6.35E-04 0.001

ppm 9.40E-01 4.91E-01 4.86E-01 0.639

ppm@7%O2 7.83E-01 4.08E-01 4.02E-01 0.531

Location: stack - Method 26

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.195 0.204 0.209 0.203

lb/mmBtuO2 1.43E-04 1.47E-04 1.46E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.2 0.208 0.204 0.204

lb/mmBtuO2 1.46E-04 1.50E-04 1.42E-04 0.000

Location: stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.004455 0.00386 0.003217 0.004

lb/mmBtuO2 5.96E-07 5.14E-07 4.17E-07 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Thursday, February 10, 2011 Page 14 of 25
Emissions Testing Unit 7

7/2/2010

Mass_mg 0.03515 0.02807 0.02503 0.029

lb/mmBtuO2 4.70E-06 3.74E-06 3.25E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00305 0.00225 0.00175 0.002

lb/mmBtuO2 4.08E-07 3.00E-07 2.27E-07 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00085 0.00084 0.00103 0.001

lb/mmBtuO2 1.14E-07 1.12E-07 1.34E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0385 0.0172 0.0155 0.024

lb/mmBtuO2 5.15E-06 2.29E-06 2.01E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.2842 0.22926 0.20112 0.238

lb/mmBtuO2 3.80E-05 3.05E-05 2.61E-05 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0085 0.006 0.00424 0.006

lb/mmBtuO2 1.14E-06 7.99E-07 5.50E-07 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.1378 0.1268 0.09383 0.119

lb/mmBtuO2 1.84E-05 1.69E-05 1.22E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 5.675 4.517 3.8518 4.681

lb/mmBtuO2 7.60E-04 6.02E-04 4.99E-04 0.001

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0336 0.0292 0.0243 0.029

lb/mmBtuO2 4.50E-06 3.89E-06 3.15E-06 0.000

Location: stack - Method 5

Thursday, February 10, 2011 Page 15 of 25
Emissions Testing Unit 7

7/2/2010

Process Run Data

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 118.6 102.2 80.2 100.333

lb/mmBtuO2 1.59E-02 1.36E-02 1.04E-02 0.013

Location: stack - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 3.19E-01 3.58E-01 3.56E-01 0.344

ppm 1.68E+02 1.88E+02 1.87E+02 181.000

ppm@7%O2 1.39E+02 1.56E+02 1.55E+02 150.000

Location: stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 4.10E-01 4.26E-01 4.41E-01 0.426

ppm 3.00E+02 3.11E+02 3.22E+02 311.000

ppm@7%O2 2.48E+02 2.58E+02 2.68E+02 258.000

Location: stack - OTM - 27/28

Compound: Total PM2.5

Average

RunNumber 1 4 3

Mass_mg 95.4 96.4 98.1 96.633

lb/mmBtuO2 1.91E-02 1.92E-02 2.06E-02 0.020

Thursday, February 10, 2011 Page 16 of 25
Emissions Testing Unit 7

7/2/2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 0

2 0

1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr

1 0

1 Unit Gross Electric Generation 0 Mwe

1 Unit Net Electric Generation 0 MWh

1 Steam Output 0 1000 lbs steam/hr

1 Average Heat Input 0 MMBtu/hr

1 Fuel Oil Firing Rate 0 Klb/hr

Run Name Value UOM Comments

Target

Value

1 None 0

1 0

1 0

1 0

Run Name Value UOM Comments

1 none 0

1 0

1 0

1 0

1 0

Thursday, February 10, 2011 Page 17 of 25
Emissions Testing Unit 7

7/2/2010

Sampling / Stack Data Results Detail

Location stack - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 18 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 23

Average

Run Number 1 2 3

Test Date 4/2/2010 4/5/2010 4/7/2010

Run Start Time 7:48:00 AM 7:40:00 AM 7:41:00 AM

Run Finish Time 4:13:00 PM 4:07:00 PM 4:08:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.259 0.259 0.259 0.259

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.03 1.03 1.03 1.030

Barometric Pressure, inches of Mercury 30.1 30 30 30.033

Average Orifice Meter Differential, inches H2O 2.43 2.35 2.41 2.397

Dry Gas Meter Volume Sampled, cubic feet 405.734 397.306 405.203 402.748

Average Dry Gas Meter Temperature, °F 95.83 93.27 94.04 94.380

Dry Gas Meter Volume Sampled, dscf 401.741 393.834 401.162 398.912

Total Moisture Liquid collected, g 1046.2 1031.4 1073.2 1,050.267

Volume of Water Vapor, standard cubic feet 49.24 48.55 50.52 49.437

Moisture Content of Stack Gas, % 10.92 10.97 11.18 11.023

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8908 0.8903 0.8882 0.890

Carbon Dioxide, % 11.6 11.9 12.4 11.967

Oxygen, % 5.4 4.8 4.9 5.033

Carbon Monoxide & Nitrogen, % 83 83.3 82.7 83.000

Fuel Factor 1.34 1.35 1.29

Dry Molecular Weight, lb/lb-Mole 30.07 30.10 30.18 30.117

Wet Molecular weight, lb/lb-Mole 28.75 28.77 28.82 28.780

Flue Gas Static Pressure, inches of H2O -0.6 -0.6 -0.6 -0.600

Absolute Flue Gas Pressure, inches of Mercury 30.06 29.96 29.96 29.993

Average Stack Gas Temperature, °F 311.79 306.21 306.46 308.153

Average Velocity Head, inches of H2O 0.8467381246

11908

0.814779409

151216

0.825595796

270544

0.829

Average Stack Gas Velocity, feet/second 62.45 61.11 61.48 61.680

Stack Cross-Sectional Area, square feet 81.180 81.180 81.180 81.180

Dry Volumetric Flow Rate, dry scfm 186,240.9 182,858.6 183,471.9 184,190.467

Actual Wet Volumetric Flue Gas Flow Rate, acfm 304,181.5 297,654.6 299,456.8 300,430.967

Percent Isokinetic of Sampling Rate, % 99.7 99.6 101.1 100.133

Percent Excess Air, % 32.7 27.9 28.9 29.833

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 122 122 122

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, February 10, 2011 Page 19 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 20 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 26

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 21 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 22 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 5

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 23 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 24 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 10, 2011 Page 25 of 25
Emissions Testing Unit 7

7/2/2010

Location stack - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 10, 2011 Page 26 of 25