### Name: Dan Giovanni

Title: Manager, Power Supply Operations an Company: Hawaiian Electric Company, Inc. Sign Date: 7/2/2010 Name: Tony Wong Title: President Company: AirKinetics Inc. Sign Date: 7/2/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## Emissions Testing Unit 7 Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Thursday, February 10, 2011 Page 1 of 25

### Emissions Testing Unit 7

7/2/2010 Facility Information: HI, Waiau 475 Kamehameha Highway

Pearl City HI 96782 Contact: Stephen Ward
Phone: (808) 543-4535
Fax: (808) 543-4511
Email: stephen.ward@heco.com Testing Company:
AirKinetics Inc.
1308 S. Allec

Anaheim CA 92805 Contact: Tony Wong
Phone: (714) 245-1945
Fax: (714) 956-2350
Email: wongt@airkineticsinc.com

Air Permit Number: 0239-01-C Permitted Source ID/Name: 7
Permitted Maximum Process Rate: 923 MMBtu/hr Max. Normal Operation Process Rate: 863 MMBtu/hr Target Process Test Rate 842 MMBtu/hr

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Electrical power generation though combustion of fossil fuels (SIC Code 4911) is the only product or process Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 1500300502 FRS #: 110000486420

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: Tangential Firing

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
stack 122 327 336 2 122 12 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 120 0 stack 2,3,7,8-TCDD Method 23 3 480 0 stack 1,2,3,7,8-PeCDD Method 23 3 480 0 stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0 stack Regulation Description Compound Limit Unit



### Thursday, February 10, 2011 Page 2 of 25

### Emissions Testing Unit 7

7/2/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.
None 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 stack OCDD Method 23 3 480 0 stack 2,3,7,8-TCDF Method 23 3 480 0 stack 1,2,3,7,8-PeCDF Method 23 3 480 0 stack 2,3,4,7,8-PeCDF Method 23 3 480 0 stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0 stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0 stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0 stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 stack OCDF Method 23 3 480 0 stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0 stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 stack 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 stack

2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0 stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0 stack 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 stack

Total organic compounds

(TOC) as Propane Method 25A 3 120 0 stack

Hydrogen Fluoride Method 26 3 60 0 stack Hydrogen Chloride Method 26 3 60 0 stack Total PM2.5 OTM - 27/28 3 367 0 stack Beryllium Method 29 3 240 0 stack Arsenic Method 29 3 240 0 stack Cadmium Method 29 3 240 0 stack Chromium Method 29 3 240 0 stack Cobalt Method 29 3 240 0 stack Lead Method 29 3 240 0 stack Manganese Method 29 3 240 0 stack Nickel Method 29 3 240 0 stack Selenium Method 29 3 240 0 stack Antimony Method 29 3 240 0 stack O2 Method 3A O2 3 120 0 stack Co2 Method 3A CO2 3 120 0 stack Filterable Particulate Method 5 3 240 0 stack Sulfur Dioxide Method 6C 3 120 0 stack Nitrogen oxides (NOx) Method 7E 3 120 0 stack



### Thursday, February 10, 2011 Page 3 of 25

### Emissions Testing Unit 7

7/2/2010

Thursday, February 10, 2011 Page 4 of 25

### Emissions Testing Unit 7

7/2/2010 Sampling / Stack Data Results Summary



### Location stack - Method 10 Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 23 Average Run Number 1 2 3
Test Date 4/2/2010 4/5/2010 4/7/2010
Run Start Time 7:48:00 AM 7:40:00 AM 7:41:00 AM

Run Finish Time 4:13:00 PM 4:07:00 PM 4:08:00 PM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 401.741 393.834 401.162 398.912 Moisture Content of Stack Gas, % 10.92 10.97 11.18 11.023 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 11.6 11.9 12.4 11.967 Oxygen, % 5.4 4.8 4.9 5.033 Average Stack Gas Temperature, °F 311.79 306.21 306.46 308.153 Dry Volumetric Flow Rate, dry scfm 186,240.9 182,858.6 183,471.9 184,190.467 Actual Wet Volumetric Flue Gas Flow Rate, acfm 304,181.5 297,654.6 299,456.8 300,430.967 Percent Isokinetic of Sampling Rate, % 99.7 99.6 101.1 100.133 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 5 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 25A Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 26 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 6 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 29 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Location stack - Method 5 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 7 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 6C Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location stack - Method 7E Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Thursday, February 10, 2011 Page 8 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - OTM - 27/28 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Thursday, February 10, 2011 Page 9 of 25

### Emissions Testing Unit 7

7/2/2010 Emissions Summary



### Location: stack - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 4.21E-04 6.59E-04 1.31E-03 0.001 ppm 5.03E-01 7.90E-01 1.57E+00 0.954 ppm@7%O2 4.19E-01 6.56E-01 1.30E+00 0.792



### Location: stack - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000127 0.0000000195 0.0000000167 0.000 lb/mmBtuO2 8.64E-13 1.30E-12 1.10E-12 0.000 ng/dscm 1.12E-03 1.75E-03 1.47E-03 0.001 ng/dscm@7%O2 1.00E-03 1.51E-03 1.28E-03 0.001


### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000151 0.0000000111 0.00000000687 0.000 lb/mmBtuO2 1.03E-12 7.41E-13 4.53E-13 0.000 ng/dscm 1.33E-03 9.95E-04 6.05E-04 0.001 ng/dscm@7%O2 1.19E-03 8.59E-04 5.26E-04 0.001


### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.00000000933 0.0000000092 0.0000000178 0.000 lb/mmBtuO2 6.34E-13 6.14E-13 1.17E-12 0.000 ng/dscm 8.20E-04 8.25E-04 1.57E-03 0.001 ng/dscm@7%O2 7.35E-04 7.12E-04 1.36E-03 0.001


### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000124 0.0000000122 0.000000014 0.000 lb/mmBtuO2 8.43E-13 8.15E-13 9.24E-13 0.000 ng/dscm 1.09E-03 1.09E-03 1.23E-03 0.001 ng/dscm@7%O2 9.77E-04 9.41E-04 1.07E-03 0.001


### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.00000000559 0.0000000069 0.00000000496 0.000 lb/mmBtuO2 3.80E-13 4.61E-13 3.27E-13 0.000 ng/dscm 4.91E-04 6.19E-04 4.37E-04 0.001 ng/dscm@7%O2 4.40E-04 5.34E-04 3.80E-04 0.000


### Compound: 1,2,3,6,7,8-HxCDD Average


### Thursday, February 10, 2011 Page 10 of 25

### Emissions Testing Unit 7

7/2/2010
RunNumber 1 2 3 Mass_mg 0.0000000115 0.0000000113 0.0000000197 0.000 lb/mmBtuO2 7.82E-13 7.55E-13 1.30E-12 0.000 ng/dscm 1.01E-03 1.01E-03 1.73E-03 0.001 ng/dscm@7%O2 9.06E-04 8.72E-04 1.50E-03 0.001


### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000102 0.00000000464 0.00000000466 0.000 lb/mmBtuO2 6.94E-13 3.10E-13 3.07E-13 0.000 ng/dscm 8.97E-04 4.16E-04 4.10E-04 0.001 ng/dscm@7%O2 8.04E-04 3.59E-04 3.56E-04 0.001


### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000112 0.000000011 0.0000000192 0.000 lb/mmBtuO2 7.62E-13 7.35E-13 1.27E-12 0.000 ng/dscm 9.85E-04 9.87E-04 1.69E-03 0.001 ng/dscm@7%O2 8.83E-04 8.52E-04 1.47E-03 0.001


### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.00000000447 0.00000000591 0.00000000594 0.000 lb/mmBtuO2 3.04E-13 3.95E-13 3.92E-13 0.000 ng/dscm 3.93E-04 5.30E-04 5.23E-04 0.000 ng/dscm@7%O2 3.52E-04 4.58E-04 4.54E-04 0.000


### Compound: 1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.00000000993 0.00000000657 0.00000000698 0.000 lb/mmBtuO2 6.75E-13 4.39E-13 4.60E-13 0.000 ng/dscm 8.73E-04 5.89E-04 6.15E-04 0.001 ng/dscm@7%O2 7.83E-04 5.09E-04 5.34E-04 0.001


### Compound: 1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000112 0.00000000791 0.0000000106 0.000 lb/mmBtuO2 7.62E-13 5.28E-13 6.99E-13 0.000 ng/dscm 9.85E-04 7.09E-04 9.33E-04 0.001 ng/dscm@7%O2 8.83E-04 6.12E-04 8.11E-04 0.001


### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.000000014 0.0000000111 0.0000000172 0.000 lb/mmBtuO2 9.52E-13 7.41E-13 1.13E-12 0.000 ng/dscm 1.23E-03 9.95E-04 1.51E-03 0.001 ng/dscm@7%O2 1.10E-03 8.59E-04 1.31E-03 0.001



### Thursday, February 10, 2011 Page 11 of 25

### Emissions Testing Unit 7

7/2/2010 Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.000000126 0.0000001584 0.0000001662 0.000 lb/mmBtuO2 8.57E-12 1.06E-11 1.10E-11 0.000 ng/dscm 1.11E-02 1.42E-02 1.46E-02 0.013 ng/dscm@7%O2 9.95E-03 1.23E-02 1.27E-02 0.012


### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.000000509 0.000000866 0.00000119 0.000 lb/mmBtuO2 3.46E-11 5.78E-11 7.85E-11 0.000 ng/dscm 4.47E-02 7.77E-02 1.05E-01 0.076 ng/dscm@7%O2 4.01E-02 6.71E-02 9.12E-02 0.066


### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.0000000429 0.0000000636 0.0000000699 0.000 lb/mmBtuO2 2.92E-12 4.25E-12 4.61E-12 0.000 ng/dscm 3.77E-03 5.70E-03 6.15E-03 0.005 ng/dscm@7%O2 3.38E-03 4.92E-03 5.34E-03 0.005


### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.0000000464 0.0000000545 0.000000074 0.000 lb/mmBtuO2 3.16E-12 3.64E-12 4.88E-12 0.000 ng/dscm 4.08E-03 4.89E-03 6.52E-03 0.005 ng/dscm@7%O2 3.66E-03 4.22E-03 5.66E-03 0.005


### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.00000125 0.0000025 0.00000337 0.000 lb/mmBtuO2 8.50E-11 1.67E-10 2.22E-10 0.000 ng/dscm 1.10E-01 2.24E-01 2.97E-01 0.210 ng/dscm@7%O2 9.86E-02 1.93E-01 2.58E-01 0.183


### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.000000047 0.0000000613 0.0000000766 0.000 lb/mmBtuO2 3.20E-12 4.09E-12 5.05E-12 0.000 ng/dscm 4.13E-03 5.50E-03 6.74E-03 0.005 ng/dscm@7%O2 3.70E-03 4.75E-03 5.86E-03 0.005


### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000038 0.00000000502 0.00000000505 0.000 lb/mmBtuO2 2.58E-13 3.35E-13 3.33E-13 0.000



### Thursday, February 10, 2011 Page 12 of 25

### Emissions Testing Unit 7

7/2/2010 ng/dscm 3.34E-04 4.50E-04 4.45E-04 0.000 ng/dscm@7%O2 3.00E-04 3.89E-04 3.87E-04 0.000


### Compound: 2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000116 0.0000000153 0.000000011 0.000 lb/mmBtuO2 7.89E-13 1.02E-12 7.26E-13 0.000 ng/dscm 1.02E-03 1.37E-03 9.68E-04 0.001 ng/dscm@7%O2 9.15E-04 1.18E-03 8.41E-04 0.001


### Compound: 2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.00000000852 0.0000000116 0.0000000133 0.000 lb/mmBtuO2 5.79E-13 7.75E-13 8.77E-13 0.000 ng/dscm 7.49E-04 1.04E-03 1.17E-03 0.001 ng/dscm@7%O2 6.72E-04 8.98E-04 1.02E-03 0.001


### Compound: 2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.00000000898 0.0000000142 0.0000000149 0.000 lb/mmBtuO2 6.11E-13 9.48E-13 9.83E-13 0.000 ng/dscm 7.89E-04 1.27E-03 1.31E-03 0.001 ng/dscm@7%O2 7.08E-04 1.10E-03 1.14E-03 0.001


### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.0000000411 0.0000000625 0.000000033 0.000 lb/mmBtuO2 2.79E-12 4.17E-12 2.18E-12 0.000 ng/dscm 3.61E-03 5.61E-03 2.91E-03 0.004 ng/dscm@7%O2 3.24E-03 4.84E-03 2.53E-03 0.004


### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.0000000499 0.0000000615 0.0000000868 0.000 lb/mmBtuO2 3.39E-12 4.11E-12 5.73E-12 0.000 ng/dscm 4.39E-03 5.52E-03 7.64E-03 0.006 ng/dscm@7%O2 3.94E-03 4.77E-03 6.64E-03 0.005


### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.000000242 0.000000328 0.000000376 0.000 lb/mmBtuO2 1.65E-11 2.19E-11 2.48E-11 0.000 ng/dscm 2.13E-02 2.94E-02 3.31E-02 0.028 ng/dscm@7%O2 1.91E-02 2.54E-02 2.88E-02 0.024


### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3



### Thursday, February 10, 2011 Page 13 of 25

### Emissions Testing Unit 7

7/2/2010 Mass_mg 0.0000000301 0.0000000683 0.000000163 0.000 lb/mmBtuO2 2.05E-12 4.56E-12 1.08E-11 0.000 ng/dscm 2.65E-03 6.13E-03 1.44E-02 0.008 ng/dscm@7%O2 2.38E-03 5.29E-03 1.25E-02 0.007


### Compound: OCDD Average RunNumber 1 2 3 Mass_mg 0.0000000308 0.0000000534 0.0000000244 0.000 lb/mmBtuO2 2.09E-12 3.57E-12 1.61E-12 0.000 ng/dscm 2.71E-03 4.79E-03 2.15E-03 0.003 ng/dscm@7%O2 2.43E-03 4.14E-03 1.87E-03 0.003


### Compound: OCDF Average RunNumber 1 2 3 Mass_mg 0.0000000173 0.000000017 0.0000000187 0.000 lb/mmBtuO2 1.18E-12 1.14E-12 1.23E-12 0.000 ng/dscm 1.52E-03 1.52E-03 1.65E-03 0.002 ng/dscm@7%O2 1.36E-03 1.31E-03 1.43E-03 0.001



### Location: stack - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 1.24E-03 6.45E-04 6.35E-04 0.001 ppm 9.40E-01 4.91E-01 4.86E-01 0.639 ppm@7%O2 7.83E-01 4.08E-01 4.02E-01 0.531



### Location: stack - Method 26 Compound: Hydrogen Chloride Average RunNumber 1 2 3 Mass_mg 0.195 0.204 0.209 0.203 lb/mmBtuO2 1.43E-04 1.47E-04 1.46E-04 0.000


### Compound: Hydrogen Fluoride Average RunNumber 1 2 3 Mass_mg 0.2 0.208 0.204 0.204 lb/mmBtuO2 1.46E-04 1.50E-04 1.42E-04 0.000



### Location: stack - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.004455 0.00386 0.003217 0.004 lb/mmBtuO2 5.96E-07 5.14E-07 4.17E-07 0.000


### Compound: Arsenic Average RunNumber 1 2 3



### Thursday, February 10, 2011 Page 14 of 25

### Emissions Testing Unit 7

7/2/2010 Mass_mg 0.03515 0.02807 0.02503 0.029 lb/mmBtuO2 4.70E-06 3.74E-06 3.25E-06 0.000


### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.00305 0.00225 0.00175 0.002 lb/mmBtuO2 4.08E-07 3.00E-07 2.27E-07 0.000


### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.00085 0.00084 0.00103 0.001 lb/mmBtuO2 1.14E-07 1.12E-07 1.34E-07 0.000


### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.0385 0.0172 0.0155 0.024 lb/mmBtuO2 5.15E-06 2.29E-06 2.01E-06 0.000


### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.2842 0.22926 0.20112 0.238 lb/mmBtuO2 3.80E-05 3.05E-05 2.61E-05 0.000


### Compound: Lead Average RunNumber 1 2 3 Mass_mg 0.0085 0.006 0.00424 0.006 lb/mmBtuO2 1.14E-06 7.99E-07 5.50E-07 0.000


### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.1378 0.1268 0.09383 0.119 lb/mmBtuO2 1.84E-05 1.69E-05 1.22E-05 0.000


### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 5.675 4.517 3.8518 4.681 lb/mmBtuO2 7.60E-04 6.02E-04 4.99E-04 0.001


### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.0336 0.0292 0.0243 0.029 lb/mmBtuO2 4.50E-06 3.89E-06 3.15E-06 0.000



### Location: stack - Method 5



### Thursday, February 10, 2011 Page 15 of 25

### Emissions Testing Unit 7

7/2/2010

Process Run Data Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 118.6 102.2 80.2 100.333 lb/mmBtuO2 1.59E-02 1.36E-02 1.04E-02 0.013



### Location: stack - Method 6C Compound: Sulfur Dioxide Average Run 1 2 3 lb/mmBtuO2 3.19E-01 3.58E-01 3.56E-01 0.344 ppm 1.68E+02 1.88E+02 1.87E+02 181.000 ppm@7%O2 1.39E+02 1.56E+02 1.55E+02 150.000



### Location: stack - Method 7E Compound: Nitrogen oxides (NOx) Average Run 1 2 3 lb/mmBtuO2 4.10E-01 4.26E-01 4.41E-01 0.426 ppm 3.00E+02 3.11E+02 3.22E+02 311.000 ppm@7%O2 2.48E+02 2.58E+02 2.68E+02 258.000



### Location: stack - OTM - 27/28 Compound: Total PM2.5 Average RunNumber 1 4 3 Mass_mg 95.4 96.4 98.1 96.633 lb/mmBtuO2 1.91E-02 1.92E-02 2.06E-02 0.020



### Thursday, February 10, 2011 Page 16 of 25

### Emissions Testing Unit 7

7/2/2010 Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value 1 0


### 2 0
1 0
2 0


### 1 0
2 0
1 0


### 2 0
1 0
2 0


### 1 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
2 Residual Oil (No. 6) Burned 0 1000 Gallons/hr
1 0


### 1 Unit Gross Electric Generation 0 Mwe
1 Unit Net Electric Generation 0 MWh
1 Steam Output 0 1000 lbs steam/hr


### 1 Average Heat Input 0 MMBtu/hr
1 Fuel Oil Firing Rate 0 Klb/hr

Run Name Value UOM Comments Target Value 

### 1 None 0
1 0
1 0


### 1 0

Run Name Value UOM Comments 1 none 0 1 0 

### 1 0 1 0 1 0



### Thursday, February 10, 2011 Page 17 of 25

### Emissions Testing Unit 7

7/2/2010 Sampling / Stack Data Results Detail



### Location stack - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 18 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 23 Average Run Number 1 2 3 Test Date 4/2/2010 4/5/2010 4/7/2010 Run Start Time 7:48:00 AM 7:40:00 AM 7:41:00 AM Run Finish Time 4:13:00 PM 4:07:00 PM 4:08:00 PM Net Traversing Points 24 24 24 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.259 0.259 0.259 0.259 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 1.03 1.03 1.03 1.030 Barometric Pressure, inches of Mercury 30.1 30 30 30.033 Average Orifice Meter Differential, inches H2O 2.43 2.35 2.41 2.397 Dry Gas Meter Volume Sampled, cubic feet 405.734 397.306 405.203 402.748 Average Dry Gas Meter Temperature, °F 95.83 93.27 94.04 94.380 Dry Gas Meter Volume Sampled, dscf 401.741 393.834 401.162 398.912 Total Moisture Liquid collected, g 1046.2 1031.4 1073.2 1,050.267 Volume of Water Vapor, standard cubic feet 49.24 48.55 50.52 49.437 Moisture Content of Stack Gas, % 10.92 10.97 11.18 11.023 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.8908 0.8903 0.8882 0.890 Carbon Dioxide, % 11.6 11.9 12.4 11.967 Oxygen, % 5.4 4.8 4.9 5.033 Carbon Monoxide & Nitrogen, % 83 83.3 82.7 83.000 Fuel Factor 1.34 1.35 1.29 Dry Molecular Weight, lb/lb-Mole 30.07 30.10 30.18 30.117 Wet Molecular weight, lb/lb-Mole 28.75 28.77 28.82 28.780 Flue Gas Static Pressure, inches of H2O -0.6 -0.6 -0.6 -0.600 Absolute Flue Gas Pressure, inches of Mercury 30.06 29.96 29.96 29.993 Average Stack Gas Temperature, °F 311.79 306.21 306.46 308.153 Average Velocity Head, inches of H2O 0.8467381246 11908 0.814779409

151216 0.825595796

270544 0.829

Average Stack Gas Velocity, feet/second 62.45 61.11 61.48 61.680 Stack Cross-Sectional Area, square feet 81.180 81.180 81.180 81.180 Dry Volumetric Flow Rate, dry scfm 186,240.9 182,858.6 183,471.9 184,190.467 Actual Wet Volumetric Flue Gas Flow Rate, acfm 304,181.5 297,654.6 299,456.8 300,430.967 Percent Isokinetic of Sampling Rate, % 99.7 99.6 101.1 100.133 Percent Excess Air, % 32.7 27.9 28.9 29.833 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 122 122 122 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Thursday, February 10, 2011 Page 19 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 20 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 26 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 21 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 29 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 22 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 5 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 23 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 6C Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 24 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Thursday, February 10, 2011 Page 25 of 25

### Emissions Testing Unit 7

7/2/2010
Location stack - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Thursday, February 10, 2011 Page 26 of 25