6481_INTERMOUNTAIN_MACT_ICR_PhaseIII_Process_Data

Test: Non-dioxin/furan Organic HAPS - short list 

Test Date: Unit 1 - 6/15/2010 Start TIMES:

End TIMES:

Unit 2 - 6/16/2010 Start TIMES:

End TIMES:

Data Collection 6/15/2010 8:00 to 6/16/2010 18:00

PI TAG ID's Unit 1 Unit 2 Units

Generation Load (gross) 1COAXI027A 2COAXI027A MWhe

Load (net) CS-U1-MW CS-U2-MW MWhe

Boiler Coal Feed 1COAXI001B 2COAXI001B tons/hr

Fuel Oil Feed 1COAXI011A 2COAXI011A klbh

Heat Input 1SGAPE0047 2SGAPE0047 mmbtu/hr

Steam Flow 1COAXI024 2COAXI024 klbh

Steam Pressure 1SGGPT0001 2SGGPT0001 psi

Steam Temp 1SGGTE0002 2SGGTE0002 F

Boiler O2 1COAXI187A 2COAXI187A %

OFA % Flow 1COAXI172B 2COAXI172B %

CEMS CO2 1SAAKK0015 2SAAKK0015 %

Flow 1SAAKK0016 2SAAKK0016 Macfh

SO2 1SAAKK0005 2SAAKK0005 lb/mmbtu

NOx 1SAAKK0007 2SAAKK0007 lb/mmbtu

HI 1SGAPE0049 2SGAPE0049 mmbtu/hr

Stack Temp 1CCCM30022 2CCCM30022 F

Fabric Filter FF dP - A Casing 1CCBA40001 2CCBA40001 inWC

FF dP - B Casing 1CCBB40001 2CCBB40001 inWC

FF dP - C Casing 1CCBC40001 2CCBC40001 inWC

FF dP - Avg

Scrubber FGD dP A Module 1CCCA30006 2CCCA30006 inWC

FGD dP B Module 1CCCB30006 2CCCB30006 inWC

FGD dP C Module 1CCCC30006 2CCCC30006 inWC

FGD dP D Module 1CCCD30006 2CCCD30006 inWC

FGD dP E Module 1CCCE30006 2CCCE30006 inWC

FGD dP F Module 1CCCF30006 2CCCF30006 inWC

dP Avg inWC

FGD pH A Module 1CCCA30008 2CCCA30008

FGD pH B Module 1CCCB30008 2CCCB30008

FGD pH C Module 1CCCC30008 2CCCC30008

FGD pH D Module 1CCCD30008 2CCCD30008

FGD pH E Module 1CCCE30008 2CCCE30008

FGD pH F Module 1CCCF30008 2CCCF30008

pH Avg
FGD A Module ON? 1CCCA00003 2CCCA00003

FGD B Module ON? 1CCCB00003 2CCCB00003

FGD C Module ON? 1CCCC00003 2CCCC00003

FGD D Module ON? 1CCCD00003 2CCCD00003

FGD E Module ON? 1CCCE00003 2CCCE00003

FGD F Module ON? 1CCCF00003 2CCCF00003

Slurry Feed A Mod 1CCCA30016 2CCCA30016 gpm

Slurry Feed B Mod 1CCCB30016 2CCCB30016 gpm

Slurry Feed C Mod 1CCCC30016 2CCCC30016 gpm

Slurry Feed D Mod 1CCCD30016 2CCCD30016 gpm

Slurry Feed E Mod 1CCCE30016 2CCCE30016 gpm

Slurry Feed F Mod 1CCCF30016 2CCCF30016 gpm

Total Feed gpm

Slurry Density 1CCCM30005 2CCCM30005 %

A Module HP Spray Am1CCCA30019 ps 2CCCA30019 ohms

A Module IP Spray Amps1CCCA30020 2CCCA30020 ohms

A Module LP Spray Amps1CCCA30021 2CCCA30021 ohms

B Module HP Spray Am1CCCB30019 ps 2CCCB30019 ohms

B Module IP Spray Amps1CCCB30020 2CCCB30020 ohms

B Module LP Spray Amps1CCCB30021 2CCCB30021 ohms

C Module HP Spray Am1CCCC30019 ps 2CCCC30019 ohms

C Module IP Spray Amps1CCCC30020 2CCCC30020 ohms

C Module LP Spray Am1CCCC30021 ps 2CCCC30021 ohms

D Module HP Spray Am1CCCD30019 ps 2CCCD30019 ohms

D Module IP Spray Amps1CCCD30020 2CCCD30020 ohms

D Module LP Spray Am1CCCD30021 ps 2CCCD30021 ohms

E Module HP Spray Am1CCCE30019 ps 2CCCE30019 ohms

E Module IP Spray Amps1CCCE30020 2CCCE30020 ohms

E Module LP Spray Amps1CCCE30021 2CCCE30021 ohms

F Module HP Spray Am1CCCF30019 ps 2CCCF30019 ohms

F Module IP Spray Amps1CCCF30020 2CCCF30020 ohms

F Module LP Spray Amps1CCCF30021 2CCCF30021 ohms

Total Spray Flow gpm

Amp to gpm conv factor 603.0846

L/G Ratio
Run 1 6/15/2010 8:13 Run 2 6/15/2010 10:55 Run 3

6/15/2010 10:28 6/15/2010 13:07

Run 1 6/16/2010 8:37 Run 2 6/16/2010 11:14 Run 3

6/16/2010 10:47 6/16/2010 13:25

Compilation of Hourly Averages

Current Values - Unit 1 Current Values - Unit 2 Conv ValuesU1 Conv Values U2

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?
#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME?

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? #NAME? #NAME? gpm

#NAME? #NAME? GPM

#NAME? #NAME? g/Mcf
6/15/2010 13:25:00 PMRun 4 6/15/2010 16:05:00 PM

6/15/2010 15:36:00 PM 6/15/2010 18:16:00 PM

6/16/2010 13:43:00 PMRun 4 6/16/2010 16:00:00 PM

6/16/2010 15:54:00 PM 6/16/2010 18:00:00 PM
PI TAG ID's Unit 1 Unit 2 Units

Boiler Coal Feed 1COAXI001B 2COAXI001B tons/hr

Fuel Oil Feed 1COAXI011A 2COAXI011A klbh

Heat Input 1SGAPE0047 2SGAPE0047 mmbtu/hr

Steam Flow 1COAXI024 2COAXI024 klbh

Steam Pressure 1SGGPT0001 2SGGPT0001 psi

Steam Temp 1SGGTE0002 2SGGTE0002 F

Boiler O2 1COAXI187A 2COAXI187A %

OFA % Flow 1COAXI172B 2COAXI172B %

Test Period Coal Feed Fuel oil feed Heat Input Steam flow Steam Pressure

Start 6/15/2010 8:00 tons/hr klbh mmbtu/hr klbh psi

Hour 1 6/15/2010 9:00 381.2524947 0.02175406 8546.354557 6658.6817 2384.231185

Hour 2 6/15/2010 10:00 381.829816 0.024524116 8558.549756 6672.3339 2383.880225

Hour 3 6/15/2010 11:00 381.13935 0.026757361 8544.364746 6688.7547 2383.714554

Hour 4 6/15/2010 12:00 380.0994714 0.026567224 8519.956071 6680.196 2384.480492

Hour 5 6/15/2010 13:00 380.4890341 0.028212339 8527.176758 6680.8673 2383.771596

Hour 6 6/15/2010 14:00 380.0935112 0.029782333 8518.912386 6701.1825 2383.315971

Hour 7 6/15/2010 15:00 379.6255844 0.031156274 8510.672314 6702.5696 2384.023512

Hour 8 6/15/2010 16:00 381.8511519 0.030901386 8554.417546 6710.6142 2380.395112

Hour 9 6/15/2010 17:00 381.993874 0.031667285 8474.30026 6702.8263 2385.585532

Hour 10 6/15/2010 18:00 379.9520254 0.034306226 8385.796794 6704.5592 2384.003533

Unit 1
Steam Temp Boiler O2 OFA % of Ttl Flow Test Period Coal Feed Fuel oil feed

F % % 6/16/2010 8:00 tons/hr klbh

1000.88606 3.327042 3.667636458 6/16/2010 9:00 384.6108 0

1002.80201 3.325867 3.698044116 6/16/2010 10:00 383.9728 0

1002.31983 3.306944 3.736438227 6/16/2010 11:00 382.6201 0

1002.74485 3.285099 3.72407415 6/16/2010 12:00 381.4983 0

1001.47638 3.374404 3.754117786 6/16/2010 13:00 382.4303 0

999.346573 3.461674 3.869214576 6/16/2010 14:00 383.0474 0

1001.22821 3.440898 3.969463765 6/16/2010 15:00 384.3265 0

1002.70875 3.360814 4.366419452 6/16/2010 16:00 385.1316 0

1001.14418 3.06422 4.344740353 6/16/2010 17:00 383.8119 0

1000.90632 3.057728 4.323908071 6/16/2010 18:00 383.1708 0
Heat Input Steam flow Steam Pressure Steam Temp Boiler O2 OFA % of Ttl Flow

mmbtu/hr klbh psi F % %

8486.978 6477.4646 2359.143587 998.110864 3.364 3.030015934

8472.079 6492.6675 2358.226172 998.547227 3.113113 3.063651917

8443.898 6497.4435 2358.008233 998.40507 3.041443 2.532282192

8420.734 6497.7089 2358.810336 998.270581 3.232783 1.967970018

8436.641 6508.4382 2356.556088 999.791545 3.352985 1.687661247

8454.884 6526.6674 2357.102624 999.278792 3.456478 1.83245254

8479.177 6522.5348 2355.826137 998.974187 3.545341 2.142100287

8496.689 6504.7405 2357.364226 999.63429 3.555353 2.532417722

8471.365 6507.3314 2358.649518 997.333562 3.409713 2.451779474

8455.391 6528.3562 2359.07142 998.945206 3.386151 1.94010114

Unit 2
PI TAG ID's Unit 1 Unit 2 Units

Generation Load (gross) 1COAXI027A 2COAXI027A MWhe

Load (net) CS-U1-MW CS-U2-MW MWhe

Test Period Load (gross) Load (net) Test Period Load (gross)

Start 6/15/2010 8:00 MWh-e MWh-e 6/16/2010 8:00 MWh-e

Hour 1 6/15/2010 9:00 949.804948 896.0168056 6/16/2010 9:00 949.9037708

Hour 2 6/15/2010 10:00 949.947644 895.673297 6/16/2010 10:00 949.9116235

Hour 3 6/15/2010 11:00 950.120235 895.5350544 6/16/2010 11:00 950.0119613

Hour 4 6/15/2010 12:00 949.902425 895.230087 6/16/2010 12:00 950.0533076

Hour 5 6/15/2010 13:00 950.127735 895.225686 6/16/2010 13:00 949.882389

Hour 6 6/15/2010 14:00 950.033252 896.4014023 6/16/2010 14:00 950.1242034

Hour 7 6/15/2010 15:00 949.940148 896.187182 6/16/2010 15:00 950.0450369

Hour 8 6/15/2010 16:00 948.811126 895.0176965 6/16/2010 16:00 949.9699095

Hour 9 6/15/2010 17:00 950.916083 896.9308529 6/16/2010 17:00 949.8823792

Hour 10 6/15/2010 18:00 949.971424 895.6325178 6/16/2010 18:00 949.9831064

Unit 1 Unit 2
Load (net)

MWh-e

890.22202

890.49628

891.28082

889.88576

887.6479

888.15193

889.02714

889.26803

889.66918

889.56413

Unit 2
PI TAG ID's Unit 1 Unit 2 Units

CEMS CO2 1SAAKK0015 2SAAKK0015 %

(Wet Basis) Flow 1SAAKK0016 2SAAKK0016 Macfh

unadjusted SO2 1SAAKK0005 2SAAKK0005 lb/mmbtu

NOx 1SAAKK0007 2SAAKK0007 lb/mmbtu

HI 1SGAPE0049 2SGAPE0049 mmbtu/hr

Stack Temp 1CCCM30022 2CCCM30022 F

Test Period CO2 Flow SO2 NOx HI Stack Temp

Start 6/15/2010 8:00 % Macfh lb/mmbtu lb/mmbtu mmbtu/hr F

Hour 1 6/15/2010 9:00 12.4981396 105.3557825 0.081499039 0.449182 8597.345 118.7076

Hour 2 6/15/2010 10:00 12.4547343 106.0869654 0.081326407 0.447964 8599.921 118.807

Hour 3 6/15/2010 11:00 12.3574531 106.2230653 0.076053703 0.445139 8599.792 118.9064

Hour 4 6/15/2010 12:00 12.2930488 106.0129772 0.076515516 0.445135 8597.571 119.0054

Hour 5 6/15/2010 13:00 12.1894095 107.0161241 0.078624504 0.451466 8601.263 119.0539

Hour 6 6/15/2010 14:00 12.1579224 106.9237934 0.075933197 0.452331 8601.379 119.0663

Hour 7 6/15/2010 15:00 12.1203489 106.2226467 0.061182424 0.453968 8599.103 119.0788

Hour 8 6/15/2010 16:00 12.1457195 105.7554371 0.058905762 0.449702 8589.74 119.0912

Hour 9 6/15/2010 17:00 12.3534257 104.4508048 0.054708037 0.41777 8607.44 119.1036

Hour 10 6/15/2010 18:00 12.3435635 104.4004669 0.053064503 0.422295 8599.158 119.116

Unit 1
Stack Temp Test Period CO2 Flow SO2 NOx HI Stack Temp

6/16/2010 8:00 % Macfh lb/mmbtu lb/mmbtu mmbtu/hr F

6/16/2010 9:00 11.59607 117.5015 0.100135 0.421529 8350.902 113.5815

6/16/2010 10:00 11.74622 116.2672 0.09213 0.403451 8351.97 113.8523

6/16/2010 11:00 11.79461 115.5037 0.088345 0.403731 8351.958 114.1232

6/16/2010 12:00 11.67481 116.8933 0.086107 0.445677 8351.884 114.394

6/16/2010 13:00 11.55097 118.0358 0.084555 0.456262 8349.821 114.6648

6/16/2010 14:00 11.49785 118.4129 0.084505 0.451142 8353.349 114.6803

6/16/2010 15:00 11.63788 118.996 0.084273 0.454502 8351.268 114.2145

6/16/2010 16:00 11.88869 119.0345 0.079616 0.445953 8351.543 113.7375

6/16/2010 17:00 11.62946 118.2631 0.081474 0.432394 8350.53 113.2605

6/16/2010 18:00 11.56509 118.0257 0.079579 0.42141 8350.09 112.7834

Unit 2
PI TAG ID's Unit 1 Unit 2 Units

Fabric Filter FF dP - A Casing 1CCBA40001 2CCBA40001 inWC

FF dP - B Casing 1CCBB40001 2CCBB40001 inWC

FF dP - C Casing 1CCBC40001 2CCBC40001 inWC

Test Period FF dP - A Casing FF dP - B Casing FF dP - C Casing AVG

Start 6/15/2010 8:00 inWC inWC inWC inWC

Hour 1 6/15/2010 9:00 8.977834706 8.4748275 7.920811564 8.45782

Hour 2 6/15/2010 10:00 9.184249802 8.686397393 8.078923508 8.64986

Hour 3 6/15/2010 11:00 9.215749038 8.776194702 8.152714517 8.71489

Hour 4 6/15/2010 12:00 9.238723417 8.790960004 8.13907111 8.72292

Hour 5 6/15/2010 13:00 9.337268501 8.959205385 8.243879555 8.84678

Hour 6 6/15/2010 14:00 9.301177915 8.909205614 8.220103476 8.81016

Hour 7 6/15/2010 15:00 9.258529748 8.842857952 8.167977926 8.75646

Hour 8 6/15/2010 16:00 9.271447222 8.829890668 8.160136047 8.75382

Hour 9 6/15/2010 17:00 9.156121656 8.64512941 8.093897197 8.63172

Hour 10 6/15/2010 18:00 9.163884014 8.778888057 8.09701254 8.67993

Unit 1
Test Period FF dP - A Casing FF dP - B Casing FF dP - C Casing AVG

6/16/2010 8:00 inWC inWC inWC inWC

6/16/2010 9:00 9.384865141 8.989931806 8.287419203 8.8874

6/16/2010 10:00 9.31561281 8.909653698 8.301763769 8.8423

6/16/2010 11:00 9.064237797 8.667520519 8.084509693 8.6054

6/16/2010 12:00 9.474314954 9.057963938 8.294565934 8.9423

6/16/2010 13:00 9.803642136 9.390987951 8.701061084 9.2986

6/16/2010 14:00 9.559209146 9.139302603 8.545535597 9.0813

6/16/2010 15:00 9.644304695 9.259388936 8.533548939 9.1457

6/16/2010 16:00 9.653440979 9.239886546 8.607567924 9.167

6/16/2010 17:00 9.005824894 8.591854855 8.063661242 8.5538

6/16/2010 18:00 9.318743607 8.889748658 8.22857679 8.8124

Unit 2
Scrubber

FGD dP A Module FGD dP B Module FGD dP C Module FGD dP D Module

Test Period 1CCCA30006 1CCCB30006 1CCCC30006 1CCCD30006

Start 6/15/2010 8:00 inWC inWC inWC inWC

Hour 1 6/15/2010 9:00 0 1.79544284 1.51255883 1.602740194

Hour 2 6/15/2010 10:00 0 1.821881406 1.526581088 1.61030037

Hour 3 6/15/2010 11:00 0 1.814119572 1.506317499 1.611550738

Hour 4 6/15/2010 12:00 0 1.828693906 1.526743465 1.608256988

Hour 5 6/15/2010 13:00 0 1.838303825 1.545495865 1.601977685

Hour 6 6/15/2010 14:00 0 1.863473788 1.551704241 1.585071421

Hour 7 6/15/2010 15:00 0 1.854672705 1.550308434 1.567225056

Hour 8 6/15/2010 16:00 0 1.837535725 1.550892326 1.549769968

Hour 9 6/15/2010 17:00 0 1.820265225 1.554000861 1.546084191

Hour 10 6/15/2010 18:00 0 1.823021654 1.542813359 1.549234507
FGD dP E Module FGD dP F Module dP Avg FGD pH A Module FGD pH B Module

1CCCE30006 1CCCF30006 1CCCA30008 1CCCB30008

inWC inWC inWC

2.024796869 0.012683238 1.7339 7.233976197 5.708333639

2.037246721 0.013965016 1.749 7.229561352 5.711268553

2.042099111 0.015246793 1.7435 7.231645287 5.712694297

2.048165724 0.01652857 1.753 7.237369984 5.716264707

2.044474929 0.017810348 1.7576 7.242674874 5.710773831

2.055327833 0.019092125 1.7639 7.246096438 5.7140307

2.058810381 0.020373903 1.7578 7.247770546 5.716625069

2.023188105 0.02118989 1.7403 7.248954432 5.713370505

1.995500392 0.021119699 1.729 7.248489579 5.71341226

2.006582043 0.021028143 1.7304 7.245125837 5.720162878
FGD pH C Module FGD pH D Module FGD pH E Module FGD pH F Module pH Avg

1CCCC30008 1CCCD30008 1CCCE30008 1CCCF30008

5.73317135 5.747941699 5.708655851 6.92424209 5.7245

5.737679529 5.751370547 5.692997415 6.90458816 5.7233

5.736211641 5.732396159 5.680812738 6.886165319 5.7155

5.776795869 5.727237375 5.646846277 6.871193417 5.7168

5.771213419 5.706744707 5.620206105 6.856461873 5.7022

5.771269229 5.730950062 5.82892814 6.841734421 5.7613

5.783561038 5.718408525 6.173774995 6.830038791 5.8481

5.791693683 5.742517963 6.020472312 6.82095723 5.817

5.805370192 5.76167168 5.871169974 6.811875669 5.7879

5.809685107 5.749119411 5.763351055 6.805494823 5.7606
FGD A Module ON? FGD B Module ON? FGD C Module ON? FGD D Module ON? FGD E Module ON?

1CCCA00003 1CCCB00003 1CCCC00003 1CCCD00003 1CCCE00003

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON

OFF ON ON ON ON
FGD F Module ON? Slurry Feed A Mod Slurry Feed B Mod Slurry Feed C Mod

1CCCF00003 1CCCA30016 1CCCB30016 1CCCC30016

gpm gpm gpm

OFF 2.748458643 19.90388988 25.18922873

OFF 0.544157231 19.10443652 23.92116792

OFF 0.467250587 18.16826292 24.80049791

OFF 0.390343943 20.95784632 12.65161211

OFF 0.313437299 25.05369504 17.87326219

OFF 0.236530656 19.37594051 20.84500448

OFF 0.159624012 20.47118544 17.95908837

OFF 0.082717368 19.42237022 24.39027164

OFF 0.012738209 21.13756335 12.98340145

OFF 0 16.43315239 20.6474166
Slurry Feed D Mod Slurry Feed E Mod Slurry Feed F Mod Total Feed Slurry Density

1CCCD30016 1CCCE30016 1CCCF30016 1CCCM30005

gpm gpm gpm gpm %

21.60316962 63.44682004 0.053066602 130.14311 31.73051497

21.57618991 62.67575165 0.056728823 127.27755 31.72084414

22.34025396 64.24606667 0.062186722 129.55508 31.7549442

22.49768831 68.82779545 0.069510992 124.93494 31.78904426

20.48242258 63.4902547 0.076835434 126.89963 31.82096914

20.5101768 98.34958297 0.084159876 159.0807 31.71712628

21.55774528 58.0240175 0.091484318 118.01204 31.31642182

20.88857228 0 0.098808761 64.701214 30.85360651

19.6222911 0 0.106133203 53.743256 31.137389

20.11774987 55.0000747 0.113457645 112.19839 31.27867599
Amp to gpm conv factor

603.0846

Limestone Feed A Module HP Spray Amps A Module IP Spray Amps

tons 1CCCA30019 1CCCA30020

lb/hr ohms ohms

24777.04707 0 0

24224.10719 0 0

24684.0863 0 0

23829.37444 0 0

24228.41613 0 0

30273.49681 0 0

22174.28831 0 0

11977.59481 0 0

10040.54799 0 0

21056.50319 0 0
A Module LP Spray Amps conv B Module HP Spray Amps B Module IP Spray Amps

1CCCA30021 1CCCB30019 1CCCB30020

ohms gpm ohms ohms

0 0 27.35453852 24.06939121

0 0 27.34767183 24.09185243

0 0 27.34080514 24.11703015

0 0 27.3339386 24.14220787

0 0 27.32707214 24.16738559

0 0 27.32020569 24.1925633

0 0 27.31333923 24.21774102

0 0 27.30647278 24.24291874

0 0 27.29960632 24.2705602

0 0 27.29273987 24.30456881
B Module LP Spray Amps conv C Module HP Spray Amps C Module IP Spray Amps

1CCCB30021 1CCCC30019 1CCCC30020

ohms gpm ohms ohms

24.40444139 45730.92 24.94326323 23.05044026

24.40215233 45738.95 24.90882093 23.00417734

24.39986328 45748.61 24.87437863 22.95791443

24.39757422 45758.27 24.83993634 22.92197181

24.39528516 45767.94 24.80549404 22.90735516

24.39299611 45777.6 24.771286 22.89338802

24.39313893 45788.73 24.77825583 22.87942087

24.42034185 45816.18 24.81551462 22.86545373

24.45506597 45849.65 24.85277341 22.85148659

24.48979008 45886.96 24.8900322 22.83751945
C Module LP Spray Amps conv D Module HP Spray Amps D Module IP Spray Amps

1CCCC30021 1CCCD30019 1CCCD30020

ohms gpm ohms ohms

23.05195889 42846.54 25.64967416 25.78409344

23.02634086 42782.42 25.66123717 25.79834854

23.00072283 42718.3 25.66341506 25.80034828

22.9751048 42660.4 25.61997928 25.80034828

22.95192252 42616.84 25.57048274 25.80034828

22.97273238 42600.33 25.5209862 25.80034828

23.00987178 42618.51 25.47148966 25.80034828

23.04701118 42654.96 25.42199311 25.80034828

23.08415058 42691.4 25.39143024 25.80034828

23.12128998 42727.85 25.42952209 25.79894415
D Module LP Spray Amps conv E Module HP Spray Amps E Module IP Spray Amps

1CCCD30021 1CCCE30019 1CCCE30020

ohms gpm ohms ohms

24.56994869 45836.67 25.83271205 24.27717376

24.50861261 45815.25 25.88547563 24.25868037

24.70978888 45939.1 25.9382392 24.24018698

24.50826967 45791.37 25.99100278 24.22169359

24.64235476 45842.38 26.04376635 24.2032002

24.64649485 45815.03 26.07667977 24.18597705

24.80915901 45883.28 26.08147175 24.17207087

24.4135841 45614.86 26.08605886 24.15833748

24.71776621 45779.88 26.09064598 24.1446041

24.54048974 45695.09 26.09523309 24.13087071
E Module LP Spray Amps conv F Module HP Spray Amps F Module IP Spray Amps

1CCCE30021 1CCCF30019 1CCCF30020

ohms gpm ohms ohms

23.4565258 44366.77 0 0

23.4565258 44387.44 0 0

23.4565258 44408.11 0 0

23.4565258 44428.77 0 0

23.4565258 44449.44 0 0

23.44847585 44454.05 0 0

23.41952368 44431.09 0 0

23.38949491 44407.47 0 0

23.35946614 44383.84 0 0

23.32943737 44360.21 0 0
F Module LP Spray Amps conv Total Spray Flow L/G Ratio

1CCCF30021

ohms gpm gpm

0.003298596 1.989333 178780.9085 101.8155

0.005759215 3.473294 178724.0584 101.0816

0.008219834 4.957255 178814.1127 101.003

0.010680453 6.441217 178638.8167 101.1039

0.013141072 7.925178 178676.5938 100.1774

0.015601691 9.409139 178647.0069 100.2473

0.011466708 6.915395 178721.6069 100.9511

0.010145979 6.118883 178493.4592 101.2677

0.021447193 12.93447 178704.7646 102.6539

0.029712099 17.91891 178670.1075 102.6835
Scrubber

FGD dP A Module FGD dP B Module FGD dP C Module FGD dP D Module

Test Period 2CCCA30006 2CCCB30006 2CCCC30006 2CCCD30006

Start 6/16/2010 8:00 inWC inWC inWC inWC

Hour 1 6/16/2010 9:00 0.176225065 0 1.678731115 1.920213483

Hour 2 6/16/2010 10:00 0.177246646 0 1.674802496 1.92079129

Hour 3 6/16/2010 11:00 0.178803091 0 1.68173353 1.921369098

Hour 4 6/16/2010 12:00 0.180359536 0 1.701339181 1.926364247

Hour 5 6/16/2010 13:00 0.181915981 0 1.697823273 1.945004581

Hour 6 6/16/2010 14:00 0.183472426 0 1.723146427 1.964610726

Hour 7 6/16/2010 15:00 0.185028871 0 1.72562208 1.981912578

Hour 8 6/16/2010 16:00 0.186585316 0 1.731092719 1.982357862

Hour 9 6/16/2010 17:00 0.187649833 0 1.71131833 1.969684203

Hour 10 6/16/2010 18:00 0.18488869 0 1.714085279 1.956011644
FGD dP E Module FGD dP F Module dP Avg FGD pH A Module FGD pH B Module

2CCCE30006 2CCCF30006 2CCCA30008 2CCCB30008

inWC inWC inWC

1.798870721 1.723608514 1.7804 6.731239261 4

1.779341456 1.713052082 1.772 6.710928713 4

1.776143348 1.71636552 1.7739 6.697331595 4

1.799547327 1.741329046 1.7921 6.682592264 4

1.820042944 1.773711383 1.8091 6.668650302 4

1.831152631 1.7643737 1.8208 6.651088306 4

1.837179858 1.766951554 1.8279 6.644309137 4

1.82900557 1.75899465 1.8254 6.652150948 4

1.813563751 1.764506399 1.8148 6.687742517 4

1.819557482 1.755312023 1.8112 6.710533319 4
FGD pH C Module FGD pH D Module FGD pH E Module FGD pH F Module pH Avg

2CCCC30008 2CCCD30008 2CCCE30008 2CCCF30008

5.898381129 5.901534957 5.878942213 5.915710232 5.8986

5.898964733 5.902012155 5.87739268 5.926069156 5.9011

5.901696034 5.909195089 5.883882767 5.926840018 5.9054

5.901169997 5.90839308 5.880749792 5.923738124 5.9035

5.898405211 5.903082266 5.880903184 5.922594533 5.9012

5.903554046 5.910462745 5.889819307 5.897229514 5.9003

5.902902574 5.902434229 5.890045449 5.888803767 5.896

5.902230133 5.899964685 5.878803368 5.879606072 5.8902

5.90233808 5.892647442 5.86168073 5.854858093 5.8779

5.902175993 5.858209168 5.84124162 5.831076346 5.8582
FGD A Module ON? FGD B Module ON? FGD C Module ON? FGD D Module ON? FGD E Module ON?

2CCCA00003 2CCCB00003 2CCCC00003 2CCCD00003 2CCCE00003

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON

OFF OFF ON ON ON
FGD F Module ON? Slurry Feed A Mod Slurry Feed B Mod Slurry Feed C Mod

2CCCF00003 2CCCA30016 2CCCB30016 2CCCC30016

gpm gpm gpm

ON 0.004172898 0.831622047 27.3832401

ON 0.01149734 0.614740029 29.69239395

ON 0.018821782 0.397858012 31.04562951

ON 0.026146224 0.180975994 31.31248469

ON 0.033470667 0.012129462 33.80154429

ON 0.040795109 0 27.42840135

ON 0.048119551 0 25.24536906

ON 0.055408388 0 24.33638397

ON 0.054422641 0 24.80611498

ON 0.047098198 0 23.0764332
Slurry Feed D Mod Slurry Feed E Mod Slurry Feed F Mod Total Feed Slurry Density

2CCCD30016 2CCCE30016 2CCCF30016 2CCCM30005

gpm gpm gpm gpm %

33.53721445 31.94280626 20.35965524 113.22292 33.35363525

31.95862095 33.09673485 1.963721551 96.711471 33.28521173

33.967953 35.29796455 7.827362041 108.13891 33.21678821

24.85409634 35.24697896 7.634504191 99.048064 33.14836469

33.4764057 31.63388201 10.37474323 109.28658 33.07994117

28.76615255 30.96672361 7.880056463 95.041334 33.01151765

37.80419535 23.12020458 9.928947885 96.098717 32.96599599

34.30628522 28.31196452 3.53432037 90.488954 32.95347433

17.2929559 25.12548861 6.387642861 73.612202 32.9412166

35.22871705 13.11388783 8.345106523 79.764145 32.92895887
Amp to gpm conv factor

603.0846

Limestone Feed A Module HP Spray Amps A Module IP Spray Amps

tons 2CCCA30019 2CCCA30020

lb/hr ohms ohms

22658.37506 0 0

19314.37079 0 0

21552.16344 0 0

19699.68812 0 0

21691.16087 0 0

18824.75204 0 0

19007.93949 0 0

17891.55255 0 0

14549.25301 0 0

15759.30142 0 0
A Module LP Spray Amps conv B Module HP Spray Amps B Module IP Spray Amps

2CCCA30021 2CCCB30019 2CCCB30020

ohms gpm ohms ohms

0 0 0 0

0 0 0 0

0 0 0 0

0 0 0 0

0 0 0 0

0 0 0 0

0 0 0 0

0 0 0 0

0 0 0 0

0 0 0 0
B Module LP Spray Amps conv C Module HP Spray Amps C Module IP Spray Amps

2CCCB30021 2CCCC30019 2CCCC30020

ohms gpm ohms ohms

0 0 25.38594651 26.33916873

0 0 25.34916073 26.41383401

0 0 25.35483874 26.47547667

0 0 25.44145942 26.49108063

0 0 25.53004271 26.50265273

0 0 25.61862601 26.51422484

0 0 25.7072093 26.52579694

0 0 25.79579259 26.53736905

0 0 25.88437588 26.54894116

0 0 25.97295918 26.56051326
C Module LP Spray Amps conv D Module HP Spray Amps D Module IP Spray Amps

2CCCC30021 2CCCD30019 2CCCD30020

ohms gpm ohms ohms

22.26726216 44623.66 26.10927549 24.58762075

22.25352901 44638.23 26.07465132 24.65287416

22.23979586 44670.54 26.04002716 24.71812757

22.24608248 44735.98 26.00540299 24.78338099

22.29909726 44828.36 25.97077882 24.8486344

22.35403057 44921.89 25.93615465 24.89283969

22.40896388 45015.42 25.92548907 24.86830881

22.46389719 45108.95 25.97322351 24.83844978

22.5188305 45202.49 26.02359644 24.80859075

22.57376381 45296.02 26.07396936 24.77873172
D Module LP Spray Amps conv E Module HP Spray Amps E Module IP Spray Amps

2CCCD30021 2CCCE30019 2CCCE30020

ohms gpm ohms ohms

23.16666015 44545.97 26.17657291 25.28526407

23.16208228 44561.68 26.18578215 25.24252506

23.1575044 44577.4 26.19499138 25.26662363

23.15292653 44593.11 26.20420061 25.29368703

23.14834865 44608.82 26.21340984 25.32075044

23.15234837 44617.01 26.22261907 25.34781384

23.17285482 44608.15 26.23182831 25.37756944

23.19377303 44631.54 26.24560923 25.44096419

23.21469124 44656.53 26.27611395 25.51445349

23.23560945 44681.52 26.30815837 25.58794278
E Module LP Spray Amps conv F Module HP Spray Amps F Module IP Spray Amps

2CCCE30021 2CCCF30019 2CCCF30020

ohms gpm ohms ohms

24.13159882 45589.24 27.71159108 24.13168415

24.06976016 45531.72 27.73210978 24.11466806

24.00792151 45514.52 27.69540939 24.18040337

23.94608286 45499.1 27.61438117 24.25389779

23.88424421 45483.68 27.53335294 24.32739221

23.82240555 45468.26 27.45232472 24.40088663

23.76060149 45454.49 27.3712965 24.47438105

23.75682907 45498.75 27.29026828 24.54787546

23.80565865 45590.92 27.20924006 24.62136988

23.85448823 45684.01 27.12995319 24.66916345
F Module LP Spray Amps conv Total Spray Flow L/G Ratio

2CCCF30021

ohms gpm gpm

25.08234175 46392.65 181151.5286 92.50174

25.09149758 46400.29 181131.921 93.47363

25.10065341 46423.32 181185.7757 94.11948

25.10980924 46424.3 181252.4881 93.0348

25.11896507 46425.28 181346.1336 92.18192

25.1281209 46426.26 181433.4154 91.93259

25.13738729 46427.3 181505.3586 91.51839

25.16783661 46441.12 181680.3744 91.57699

25.21407357 46464.46 181914.3999 92.2931

25.26031052 46473.35 182134.9043 92.59079
AS FIRED COAL SAMPLE ANALYSES - IPSC FUELS LAB

Dry Dry Dry Dry Dry Dry Dry Dry A/R Fixed Dry Fixed

AFS ID Date Sample ID Moist% Ash% Volatile% S% Btu/lb Res Mois% C% H% N% O% Ash% S% C% H% N% O% Btu/lb MAF BTU Volatile Carbon Carbon

1ST CUT 16:30-19:00 6/14/2010 45428 8.85 12.72 37.36 0.64 11202 1.99 62.73 4.45 1.31 9.30 13.96 0.70 68.82 4.88 1.44 10.20 12290 14283 40.99 41.07 45.06

2ND CUT 19:00-22:00 6/14/2010 45429 8.72 12.82 37.52 0.65 11216 2.02 62.81 4.50 1.35 9.15 14.04 0.71 68.81 4.93 1.48 10.02 12287 14295 41.10 40.94 44.85

3RD CUT 22:00-01:00 6/14-15/10 45430 8.34 13.84 36.76 0.60 11085 2.00 62.25 4.45 1.32 9.20 15.10 0.65 67.91 4.85 1.44 10.04 12094 14244 40.10 41.06 44.80

4TH CUT 01:00-04:00 6/15/2010 45431 7.44 13.84 37.65 0.70 11231 2.24 62.73 4.47 1.33 9.49 14.95 0.76 67.77 4.83 1.44 10.25 12134 14267 40.68 41.07 44.37

1ST CUT 16:15-19:00 6/15/2010 45436 8.00 13.62 37.46 0.70 11196 1.88 62.44 4.46 1.33 9.45 14.80 0.76 67.87 4.85 1.45 10.27 12170 14284 40.72 40.92 44.48

2ND CUT 19:00-22:00 6/15/2010 45437 6.62 14.73 36.64 0.79 11397 1.52 63.39 4.48 1.42 8.57 15.77 0.85 67.88 4.80 1.52 9.18 12205 14491 39.24 42.01 44.99

3RD CUT 22:00-01:00 6/15-16/10 45438 5.82 15.24 36.35 0.88 11514 1.28 64.13 4.52 1.48 7.93 16.18 0.93 68.09 4.80 1.57 8.42 12226 14586 38.60 42.59 45.22

4TH CUT 01:00-04:00 6/16/2010 45439 6.19 14.49 36.52 0.84 11592 1.40 64.68 4.68 1.48 7.64 15.45 0.90 68.95 4.99 1.58 8.14 12357 14614 38.93 42.8 45.62

5TH CUT 04:00-06:00 6/16/2010 45440 6.21 14.90 37.16 0.90 11479 1.48 64.17 4.65 1.47 7.70 15.89 0.96 68.42 4.96 1.57 8.21 12239 14551 39.62 41.73 44.49

41