Instructions for completing the Fuel Material Analysis Information

This Information Collection Request (ICR) spreadsheet is intended to collect information about chemical analyses of fuels used fossil fuel burning power plants. Constituents of concern are: mercury, chlorine, fluorine, and metals, such as antimony, beryllium, cadmium, chromium, cobalt, lead, manganese, nickel, and selenium. This spreadsheet is intended to be used for one boiler of one facility but is designed to allow multiple (up to 4) fuel analyses at that specific boiler. This number of analyses would coincide with one boiler where emissions testing for all 4 HAP surrogates were being tested. Data for multiple boilers should be handled by using separate spreadsheets. Fields that are highlighted in yellow are required fields. Green highlighted cells should be filled using the drop

-down boxes, included. Gray fields are automatically filled from other fields.

Please name each resulting spreadsheet with the following naming convention: [FacilityID]_Unit_[BoilerID]_Fuels_Testing.xls(example: 8100_Unit_2_Fuels_Testing.xls).

Please refer to the following steps when using these spreadsheets.

1. Please enter the EIA Facility Code, Facility Name and Boiler ID of your boiler on the Boiler Information worksheet. 2. Please enter the test date on the Boiler Information worksheet. 3. Please choose the type of fuel being sampled using the drop

-down in the fuel column of the Boiler Information worksheet.If you choose "other", please provide a description of the fuel in the Other Fuel Description column. 4. Please provide the analysis method for each constituent in the Analysis Methods worksheet. For example: "ASTM D5865

- 04". 5. Please check the Units of Measure tables for HHV, Metals, and Cl/Fl in the Picklist worksheet (orange tab). If the units of measure that you plan to report are not found in the Units of measure table, please fill them in the blank, orange highlighted, cell in each table. This allows you to choose the units of measure in the Fuels Sample Results worksheet. 6. Select the HAPs Test Group (i.e., HAP surrogate) for which the tab's data reflects (orange highlighted cell)

. 7. Provide the Sample Number and Sample Date on the Fuels Sample Results worksheet. You must provide a minimum of 3 composite samples consisting of 3 combined grab samples each, but you are not limited to that number if you have collected

more. 8. Provide the results of the analyses for each constituent requested. Use the drop

-down boxes to fill in the units of

measure.EIA

Facility Code Facility Name Boiler ID Fuel Type 1

3161 EDDYSTONE 2 bituminousFuel Type 2 Fuel Type 3 Other Fuel DescriptionEIA

Facility Code Facility Name Boiler ID Basis Analyte

3161 EDDYSTONE 2 As Received Higher Heating Value 3161 EDDYSTONE 2 As Received % Moisture 3161 EDDYSTONE 2 As Received % Ash 3161 EDDYSTONE 2 As Received % Sulfur 3161 EDDYSTONE 2 Dry basis Higher Heating Value 3161 EDDYSTONE 2 Dry basis % Ash 3161 EDDYSTONE 2 Dry basis % Sulfur 3161 EDDYSTONE 2 Dry basis Antimony 3161 EDDYSTONE 2 Dry basis Arsenic 3161 EDDYSTONE 2 Dry basis Beryllium 3161 EDDYSTONE 2 Dry basis Cadmium 3161 EDDYSTONE 2 Dry basis Chlorine 3161 EDDYSTONE 2 Dry basis Chromium 3161 EDDYSTONE 2 Dry basis Cobalt 3161 EDDYSTONE 2 Dry basis Fluorine 3161 EDDYSTONE 2 Dry basis Lead 3161 EDDYSTONE 2 Dry basis Manganese 3161 EDDYSTONE 2 Dry basis Mercury 3161 EDDYSTONE 2 Dry basis Nickel 3161 EDDYSTONE 2 Dry basis SeleniumAnalysis Method for each Analyte

(example: ASTM D5865-04) ASTM D 5865-07 ASTM D 3302-09 ASTM D 3174-04 ASTM D 4239-08 Test Method B ASTM D 5865-07 ASTM D 3174-04 ASTM D 4239-08 Test Method B ASTM D 6357-04A ASTM D 6357-04A ASTM D 6357-04A ASTM D 6357-04A ASTM D4208-02 ASTM D 6357-04A ASTM D 6357-04A ASTM D3761-96 ASTM D 6357-04A ASTM D 6357-04A ASTM D 6357-04A ASTM D 6357-04A ASTM D 6357-04AEIA

Facility Code Facility

Name Boiler ID HAPs Test Group 3161 EDDYSTONE 2 Acid gas HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 001A 6/29/2010 6/29/2010 12398.00 Btu/lb 0002A 6/29/2010 6/29/2010 12037.00 Btu/lb 0003A 6/29/2010 6/29/2010 12004.00 Btu/lb 0004A 6/29/2010 6/29/2010 11870.00 Btu/lb Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 9.2 7.33 1.53 13654 Btu/lb 8.07 1.69 10.84 8.05 1.17 13501 Btu/lb 9.03 1.31 11.51 7.28 0.96 13565 Btu/lb 8.23 1.09 11.4 7.98 1.04 13397 Btu/lb 9.01 1.17Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units Antimony

(Dry Basis) Antimony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis) 881 ppm

544 ppm 560 ppmBeryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

UnitsNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 63 ppm 9.2 10.84 44 ppm 11.51 40 ppm 11.4 Proximate Analy

ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles Ash Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur 38.2 8.07 53.73 75.24 5.02 1.24 1.69 37.76 9.03 53.21 74.91 4.94 1.21 1.31 37.63 8.23 54.14 74.96 5.08 1.24 1.09 39.35 9.01 51.64 74.22 5.01 1.22 1.17 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtOxygen

8.74 8.6 9.4 9.37EIA

Facility Code Facility

Name Boiler ID HAPs Test Group 3161 EDDYSTONE 2 Dioxin/furan HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating

Value (HHV) (as received) HHV Units 001A 6/29/2010 6/29/2010 12398.00 Btu/lb 0002A 6/29/2010 6/29/2010 12037.00 Btu/lb 0003A 6/29/2010 6/29/2010 12004.00 Btu/lb 0004A 6/29/2010 6/29/2010 11870.00 Btu/lb 0005A 6/30/2010 6/30/2010 12526.00 Btu/lb 0006A 6/30/2010 6/30/2010 12246.00 Btu/lb 0007A 6/30/2010 6/30/2010 12393.00 Btu/lb 0008A 6/30/2010 6/30/2010 12046.00 Btu/lb 0011A 6/30/2010 6/30/2010 12130.00 Btu/lb 0014A 7/1/2010 7/1/2010 12061.00 Btu/lb 0015A 7/1/2010 7/1/2010 12050.00 Btu/lb 0016A 7/1/2010 7/1/2010 12001.00 Btu/lb 0019A 7/1/2010 7/1/2010 11897.00 Btu/lb Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 9.2 7.33 1.53 13654 Btu/lb 8.07 1.69 10.84 8.05 1.17 13501 Btu/lb 9.03 1.31 11.51 7.28 0.96 13565 Btu/lb 8.23 1.09 11.4 7.98 1.04 13397 Btu/lb 9.01 1.17 8.46 7.16 1.33 13684 Btu/lb 7.82 1.45 10.13 8.03 1.03 13626 Btu/lb 8.93 1.15 9.2 7.59 1.37 13649 Btu/lb 8.36 1.51 10.56 7.69 0.91 13468 Btu/lb 8.6 1.02 10.09 8.26 1.02 13491 Btu/lb 9.19 1.14 10.51 7.36 0.98 13477 Btu/lb 8.22 1.09 10.42 7.86 0.99 13452 Btu/lb 8.77 1.11 10.43 7.75 0.99 13399 Btu/lb 8.65 1.1 10.76 8.13 0.97 13332 Btu/lb 9.11 1.09Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units Antimony

(Dry Basis) Antimony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis) 881 ppm

544 ppm 560 ppm 0.09 μg/g 0.6 μg/g 5.63 μg/g 0.92

0.07 μg/g 0.65 μg/g 3.85 μg/g 0.73

0.07 μg/g 0.72 μg/g 3.52 μg/g 0.72 0.06 μg/gBeryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units

μg/g 0.18 μg/g 13.13 μg/g 4.23 μg/g 24.8 μg/g μg/g 0.18 μg/g 14.75 μg/g 4.79 μg/g

μg/g 0.18 μg/g 12.67 μg/g 4.51 μg/g 41.21 μg/gNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units 63 ppm

44 ppm 40 ppm 9.57 μg/g 1.99 μg/g 3.36 μg/g 12.71 μg/g 2.84 μg/g 2.91 μg/g

9.42 μg/g 3.5 μg/g 2.95 μg/gNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Total Moisture Volatiles Ash Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur

9.2 38.2 8.07 53.73 75.24 5.02 1.24 1.69 10.84 37.76 9.03 53.21 74.91 4.94 1.21 1.31 11.51 37.63 8.23 54.14 74.96 5.08 1.24 1.09 11.4 39.35 9.01 51.64 74.22 5.01 1.22 1.17 8.46 37.74 7.82 54.44 75.82 5.05 1.22 1.45 10.13 36.92 8.93 54.15 75.97 4.95 1.21 1.15 9.2 37.13 8.36 54.51 76.13 5.01 1.23 1.51 10.56 37.05 8.6 54.35 75.04 4.97 1.23 1.02 10.09 37.55 9.19 53.26 74.68 4.93 1.23 1.14 10.51 37.26 8.22 54.52 75.28 4.98 1.18 1.09 10.42 37.21 8.77 54.02 74.84 4.95 1.23 1.11 10.43 38.58 8.65 52.77 74.97 4.99 1.19 1.1 10.76 37.1 9.11 53.79 74.8 4.96 1.23 1.09 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Oxygen 8.74 8.6 9.4 9.37 8.64 7.79 7.76 9.14 8.83 9.25 9.1 9.1 8.81EIA

Facility Code Facility

Name Boiler ID HAPs Test Group 3161 EDDYSTONE 2 Mercury and non-mercury metalic HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date (MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 0005A 6/30/2010 6/30/2010 12526.00 Btu/lb 0006A 6/30/2010 6/30/2010 12246.00 Btu/lb 0007A 6/30/2010 6/30/2010 12393.00 Btu/lb 0008A 6/30/2010 6/30/2010 12046.00 Btu/lb 0011A 6/30/2010 6/30/2010 12130.00 Btu/lb 0014A 7/1/2010 7/1/2010 12061.00 Btu/lb 0015A 7/1/2010 7/1/2010 12050.00 Btu/lb 0016A 7/1/2010 7/1/2010 12001.00 Btu/lb 0019A 7/1/2010 7/1/2010 11897.00 Btu/lb Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 8.46 7.16 1.33 13684 Btu/lb 7.82 1.45 10.13 8.03 1.03 13626 Btu/lb 8.93 1.15 9.2 7.59 1.37 13649 Btu/lb 8.36 1.51 10.56 7.69 0.91 13468 Btu/lb 8.6 1.02 10.09 8.26 1.02 13491 Btu/lb 9.19 1.14 10.51 7.36 0.98 13477 Btu/lb 8.22 1.09 10.42 7.86 0.99 13452 Btu/lb 8.77 1.11 10.43 7.75 0.99 13399 Btu/lb 8.65 1.1 10.76 8.13 0.97 13332 Btu/lb 9.11 1.09Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units Antimony

(Dry Basis) Antimony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis) 0.09 μg/g 0.6 μg/g 5.63 μg/g 0.92 0.07 μg/g 0.65 μg/g 3.85 μg/g 0.73

0.07 μg/g 0.72 μg/g 3.52 μg/g 0.72 0.06 μg/gBeryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units μg/g 0.18 μg/g 13.13 μg/g 4.23 μg/g 24.8 μg/g μg/g 0.18 μg/g 14.75 μg/g 4.79 μg/g

μg/g 0.18 μg/g 12.67 μg/g 4.51 μg/g 41.21 μg/gNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 9.57 μg/g 1.99 μg/g 3.36 μg/g 8.46 12.71 μg/g 2.84 μg/g 2.91 μg/g 10.13 9.2 10.56 10.09 10.51 9.42 μg/g 3.5 μg/g 2.95 μg/g 10.42 10.43 10.76 Proximate Analy

ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles Ash Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur Oxygen 37.74 7.82 54.44 75.82 5.05 1.22 1.45 8.64 36.92 8.93 54.15 75.97 4.95 1.21 1.15 7.79 37.13 8.36 54.51 76.13 5.01 1.23 1.51 7.76 37.05 8.6 54.35 75.04 4.97 1.23 1.02 9.14 37.55 9.19 53.26 74.68 4.93 1.23 1.14 8.83 37.26 8.22 54.52 75.28 4.98 1.18 1.09 9.25 37.21 8.77 54.02 74.84 4.95 1.23 1.11 9.1 38.58 8.65 52.77 74.97 4.99 1.19 1.1 9.1 37.1 9.11 53.79 74.8 4.96 1.23 1.09 8.81 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtEIA

Facility Code Facility

Name Boiler ID HAPs Test Group 3161 EDDYSTONE 2 Non-dioxin/furan organic HAPs

Sample Number (minimum of 3 composite samples) Test Start Date

(MM/DD/YYYY) Test Stop Date

(MM/DD/YYYY) Higher Heating Value (HHV) (as received) HHV Units 0014A 7/1/2010 7/1/2010 12061.00 Btu/lb 0015A 7/1/2010 7/1/2010 12050.00 Btu/lb 0016A 7/1/2010 7/1/2010 12001.00 Btu/lb 0019A 7/1/2010 7/1/2010 11897.00 Btu/lb 0020A 7/2/2010 7/2/2010 12054.00 Btu/lb 0021A 7/2/2010 7/2/2010 12480.00 Btu/lb Fuel Testing Results% Moisture

(as received) % A

sh (as received) % Sulfur

(as received) Higher

Heating Value (HHV) (Dry Basis) HHV Units % A sh (Dry Basis) % Sulfur

(Dry Basis) 10.51 7.36 0.98 13477 Btu/lb 8.22 1.09 10.42 7.86 0.99 13452 Btu/lb 8.77 1.11 10.43 7.75 0.99 13399 Btu/lb 8.65 1.1 10.76 8.13 0.97 13332 Btu/lb 9.11 1.09 10.84 7.66 0.9 13520 Btu/lb 8.59 1.01 8.58 7.75 1.46 13651 Btu/lb 8.48 1.6Chlorine

(Dry Basis) Chlorine

Units Mercury

(Dry Basis) Mercury

Units Antimony

(Dry Basis) Antimony

Units Arsenic (Dry

Basis) Arsenic

Units Beryllium

(Dry Basis)

0.07 μg/g 0.72 μg/g 3.52 μg/g 0.72 0.06 μg/gBeryllium

Units Cadmium

(Dry Basis) Cadmium

Units Chromium

(Dry Basis) Chromium

Units Lead (Dry

Basis) Lead Units Manganese (Dry Basis) Manganese

Units

μg/g 0.18 μg/g 12.67 μg/g 4.51 μg/g 41.21 μg/gNickel (Dry

Basis) Nickel Units Selenium (Dry Basis) Selenium

Units Fluorine

(Dry Basis) Fluorine

Units Cobalt (Dry

Basis) Cobalt Units Total Moisture 10.51 9.42 μg/g 3.5 μg/g 2.95 μg/g 10.42 10.43 10.76 10.84 8.58 Proximate Analy ses, % by

wtNote the Proximate/Ultimate data below should be recorded on a dry basis (including ash).

Volatiles Ash Fixed Carbon Carbon Hydrogen Nitrogen Total Sulfur Oxygen 37.26 8.22 54.52 75.28 4.98 1.18 1.09 9.25 37.21 8.77 54.02 74.84 4.95 1.23 1.11 9.1 38.58 8.65 52.77 74.97 4.99 1.19 1.1 9.1 37.1 9.11 53.79 74.8 4.96 1.23 1.09 8.81 37.15 8.59 54.26 74.91 4.97 1.19 1.01 9.33 37.74 8.48 53.78 75.63 4.99 1.22 1.6 8.08 Proximate Analy

ses, % by

wt Ultimate Analy ses, % by

wtUnits of Measure Tables: Please do not modify these tables, except to add your own unit of measure to the

Fuel Units of Measure - HHV anthracite Btu/lb bituminous Btu/gallon subbituminous lignite coal refuse (culm or gob) No.2 Fuel Oil (distillate) No.6 Fuel Oil (residual or bunker C) Units of Measure - Metals synfuel mg/g petroleum coke μg/g other mg/KgUnits of Measure Tables: Please do not modify these tables, except to add your own unit of measure to the orangehightlighted cell, if necessary

.

Units of Measure - Cl, Fl % ppm