Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, February 03, 2011 Page 1 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Facility Information:

Santee Cooper - Cross Generating Station

553 Cross Station Road

Pineville SC 29468

Contact: Julie Metts, P.E.

Phone: 843-761-8000, ext. 4688

Fax: 843-761-4156

Email: jjmetts@santeecooper.com

Testing Company:

GEL Engineering, LLC

2040 Savage Road

Charleston SC 29417

Contact:Craig McKenzie

Phone: 843-769-7378

Fax: 843-769-7397

Email:

Air Permit Number:

0420-0030-Bo1

Permitted Source ID/Name:

Unit 1 Coal Fired Boiler

Permitted Maximum Process Rate: Max. Normal Operation Process Rate:

5200 MMBTu/hr with steam

Target Process Test Rate

5200 MMBTu/hr with steam

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Coal-fired boiler for electric generation, LNB, SCR, ESP, & FGD

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4501500030 FRS #: 4911

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

stack exhaust 264 0 0 0 4368 1488 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

stack exhaust Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Propane

stack exhaust Method 25A 3 120 0

stack exhaust Hydrogen Chloride Method 26A 3 180 0

stack exhaust Hydrogen Fluoride Method 26A 3 180 0

stack exhaust Manganese Method 29 3 240 0

Regulation Description Compound Limit Unit

NA 0

Thursday, February 03, 2011 Page 2 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

NA

stack exhaust Nickel Method 29 3 240 0

stack exhaust Cadmium Method 29 3 240 0

stack exhaust Lead Method 29 3 240 0

stack exhaust Antimony Method 29 3 240 0

stack exhaust Arsenic Method 29 3 240 0

stack exhaust Cobalt Method 29 3 240 0

stack exhaust Beryllium Method 29 3 240 0

stack exhaust Chromium Method 29 3 240 0

stack exhaust Selenium Method 29 3 240 0

Organic Condensible 

Particulate

stack exhaust Method 5/OTM-28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

stack exhaust Method 5/OTM-28 3 240 0

stack exhaust Total Particulate Method 5/OTM-28 3 240 0

Thursday, February 03, 2011 Page 3 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Sampling / Stack Data Results Summary

Location stack exhaust - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location stack exhaust - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Thursday, February 03, 2011 Page 4 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Location stack exhaust - Method 26A

Average

Run Number 1 2 3

Test Date 5/2/2010 5/3/2010 5/3/2010

Run Start Time 3:10:00 PM 9:05:00 

AM

1:10:00 PM

Run Finish Time 5:55:00 PM 11:50:00 

AM

3:55:00 PM

Net Run Time, minutes 180 180 180

Dry Gas Meter Volume Sampled, dscf 96.556 98.090 95.913 96.853

Moisture Content of Stack Gas, % 13.84 14.07 14.06 13.990

Moisture Saturation at Stack Gas Temperature, % 23.59 24.00 23.41 23.667

Carbon Dioxide, % 11.31 11.2 10.92 11.143

Oxygen, % 8.31 8.35 8.5 8.387

Average Stack Gas Temperature, °F 147.25 147.92 146.92 147.363

Dry Volumetric Flow Rate, dry scfm 1,632,057.8 1,646,790.0 1,622,098.2 1,633,648.66

7

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,179,986.7 2,208,724.8 2,171,775.9 2,186,829.13

3

Percent Isokinetic of Sampling Rate, % 101.8 102.5 101.8 102.033

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Thursday, February 03, 2011 Page 5 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Location stack exhaust - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location stack exhaust - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Thursday, February 03, 2011 Page 6 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Emissions Summary

Location: stack exhaust - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

Elb/hr 2.39E+03 2.75E+03 2.33E+03 2,490.000

lb/mmBtuO2 3.99E-01 4.62E-01 3.93E-01 0.418

ppm 3.38E+02 3.90E+02 3.28E+02 352.000

ppm@7%O2 3.73E+02 4.32E+02 3.68E+02 391.000

Location: stack exhaust - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

Elb/hr 3.23E+01 2.04E+01 1.93E+01 24.000

lb/mmBtuO2 5.41E-03 3.48E-03 3.26E-03 0.004

ppm 2.91E+00 1.85E+00 1.73E+00 2.163

ppm@7%O2 3.21E+00 2.07E+00 1.94E+00 2.407

Location: stack exhaust - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.918 0.626 0.427 0.657

Elb/hr 2.05E+00 1.39E+00 9.55E-01 1.465

gr/dscf 1.47E-04 9.85E-05 6.87E-05 0.000

lb/mmBtuO2 3.40E-04 2.29E-04 1.62E-04 0.000

mg/dscm 3.36E-01 2.25E-01 1.57E-01 0.239

mg/dscm@7%O2 3.71E-01 2.49E-01 1.76E-01 0.265

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.313 0.336 0.334 0.328

Elb/hr 7.00E-01 7.46E-01 7.47E-01 0.731

gr/dscf 5.00E-05 5.29E-05 5.37E-05 0.000

lb/mmBtuO2 1.16E-04 1.23E-04 1.27E-04 0.000

mg/dscm 1.14E-01 1.21E-01 1.23E-01 0.119

mg/dscm@7%O2 1.26E-01 1.34E-01 1.38E-01 0.133

Location: stack exhaust - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.000675 0.00143 0.000728 0.001

Elb/hr 1.15E-03 2.51E-03 1.25E-03 0.002

gr/dscf 8.00E-08 1.78E-07 8.63E-08 0.000

lb/mmBtuO2 1.86E-07 4.17E-07 2.04E-07 0.000

mg/dscm 1.83E-04 4.06E-04 1.97E-04 0.000

mg/dscm@7%O2 2.02E-04 4.54E-04 2.22E-04 0.000

Thursday, February 03, 2011 Page 7 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.01843 0.01502 0.02058 0.018

Elb/hr 3.15E-02 2.64E-02 3.55E-02 0.031

gr/dscf 2.19E-06 1.87E-06 2.44E-06 0.000

lb/mmBtuO2 5.07E-06 4.38E-06 5.78E-06 0.000

mg/dscm 5.00E-03 4.27E-03 5.58E-03 0.005

mg/dscm@7%O2 5.52E-03 4.77E-03 6.30E-03 0.006

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.000054 0.00005 0.00005 0.000

Elb/hr 9.24E-05 8.78E-05 8.62E-05 0.000

gr/dscf 6.40E-09 6.21E-09 5.92E-09 0.000

lb/mmBtuO2 1.49E-08 1.46E-08 1.40E-08 0.000

mg/dscm 1.47E-05 1.42E-05 1.36E-05 0.000

mg/dscm@7%O2 1.62E-05 1.59E-05 1.53E-05 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00055 0.000305 0.00034 0.000

Elb/hr 9.41E-04 5.36E-04 5.86E-04 0.001

gr/dscf 6.52E-08 3.79E-08 4.03E-08 0.000

lb/mmBtuO2 1.51E-07 8.90E-08 9.55E-08 0.000

mg/dscm 1.49E-04 8.67E-05 9.22E-05 0.000

mg/dscm@7%O2 1.65E-04 9.70E-05 1.04E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.02375 0.04595 0.03167 0.034

Elb/hr 4.06E-02 8.07E-02 5.46E-02 0.059

gr/dscf 2.82E-06 5.71E-06 3.75E-06 0.000

lb/mmBtuO2 6.54E-06 1.34E-05 8.89E-06 0.000

mg/dscm 6.44E-03 1.31E-02 8.59E-03 0.009

mg/dscm@7%O2 7.12E-03 1.46E-02 9.69E-03 0.010

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00141 0.00318 0.000551 0.002

Elb/hr 2.41E-03 5.58E-03 9.50E-04 0.003

gr/dscf 1.67E-07 3.95E-07 6.53E-08 0.000

lb/mmBtuO2 3.88E-07 9.28E-07 1.55E-07 0.000

mg/dscm 3.83E-04 9.04E-04 1.49E-04 0.000

mg/dscm@7%O2 4.23E-04 1.01E-03 1.68E-04 0.001

Compound: Lead

Average

RunNumber 1 2 3

Thursday, February 03, 2011 Page 8 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Mass_mg 0.00483 0.00202 0.00509 0.004

Elb/hr 8.26E-03 3.55E-03 8.77E-03 0.007

gr/dscf 5.73E-07 2.51E-07 6.03E-07 0.000

lb/mmBtuO2 1.33E-06 5.89E-07 1.43E-06 0.000

mg/dscm 1.31E-03 5.74E-04 1.38E-03 0.001

mg/dscm@7%O2 1.45E-03 6.42E-04 1.56E-03 0.001

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.1147 0.0128 0.01337 0.047

Elb/hr 1.96E-01 2.25E-02 2.30E-02 0.081

gr/dscf 1.36E-05 1.59E-06 1.58E-06 0.000

lb/mmBtuO2 3.16E-05 3.73E-06 3.75E-06 0.000

mg/dscm 3.11E-02 3.64E-03 3.63E-03 0.013

mg/dscm@7%O2 3.44E-02 4.07E-03 4.10E-03 0.014

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0204 0.0168 0.01906 0.019

Elb/hr 3.49E-02 2.95E-02 3.29E-02 0.032

gr/dscf 2.42E-06 2.09E-06 2.26E-06 0.000

lb/mmBtuO2 5.61E-06 4.90E-06 5.35E-06 0.000

mg/dscm 5.54E-03 4.77E-03 5.17E-03 0.005

mg/dscm@7%O2 6.12E-03 5.33E-03 5.83E-03 0.006

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.139 0.1307 0.2099 0.160

Elb/hr 2.38E-01 2.30E-01 3.62E-01 0.277

gr/dscf 1.65E-05 1.62E-05 2.49E-05 0.000

lb/mmBtuO2 3.83E-05 3.81E-05 5.89E-05 0.000

mg/dscm 3.77E-02 3.71E-02 5.69E-02 0.044

mg/dscm@7%O2 4.17E-02 4.15E-02 6.42E-02 0.049

Location: stack exhaust - Method 5/OTM-28

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 11.1 66.7 12.1 29.967

Elb/hr 1.90E+01 1.15E+02 2.07E+01 51.567

gr/dscf 1.31E-03 8.04E-03 1.43E-03 0.004

lb/mmBtuO2 3.04E-03 1.89E-02 3.38E-03 0.008

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 10.5 9.5 11.9 10.633

Elb/hr 1.80E+01 1.63E+01 2.04E+01 18.233

gr/dscf 1.24E-03 1.15E-03 1.40E-03 0.001

lb/mmBtuO2 2.88E-03 2.69E-03 3.32E-03 0.003

Thursday, February 03, 2011 Page 9 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Process Run Data

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 8.9 6.4 8.3 7.867

Elb/hr 1.52E+01 1.10E+01 1.42E+01 13.467

gr/dscf 1.05E-03 7.71E-04 9.78E-04 0.001

lb/mmBtuO2 2.44E-03 1.81E-03 2.32E-03 0.002

Thursday, February 03, 2011 Page 10 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 5855 EPA Methods 

5,10, 29; 5/4/10; 

7:45am -11:53am

5200

1 Net Electric Output 589.3 MW EPA Methods 5, 

10, 29; 5/4/10; 

7:45am -11:53am

580

1 Gross Electric Output 629.9 MW EPA Methods 5, 

10, 29; 5/4/10; 

7:45am -11:53am

610

1 Steam Output 5E+06 lbs/hr EPA Methods 5, 

10, 29; 5/4/10; 

7:45am -11:53am

4E+06

1 Feed Rate 460.85 kpph EPA Methods 5, 

10, 29; 5/4/10; 

7:45am -11:53am

450

2 Heat Input Million Btus/million BTU using O2 5833 EPA Methods 

5,10, 29; 5/4/10; 

12:45pm-4:54pm

5200

2 Net Electric Output 590.1 MW EPA Methods 

5,10, 29; 5/4/10; 

12:45pm-4:54pm

580

2 Gross Electric Output 629.7 MW EPA Methods 

5,10, 29; 5/4/10; 

12:45pm-4:54pm

610

2 Steam Output 4E+06 lbs/hr EPA Methods 

5,10, 29; 5/4/10; 

12:45pm-4:54pm

4E+06

2 Feed Rate 459 kpph EPA Methods 

5,10, 29; 5/4/10; 

12:45pm-4:54pm

450

3 Heat Input Million Btus/million BTU using O2 5853 EPA Methods 

5,10, 29; 5/4/10; 

5:15pm-9:23pm

5200

3 Net Electric Output 590 MW EPA Methods 

5,10, 29; 5/4/10; 

5:15pm-9:23pm

580

3 Gross Electric Output 630 MW EPA Methods 

5,10, 29; 5/4/10; 

5:15pm-9:23pm

610

3 Steam Output 5E+06 lbs/hr EPA Methods 

5,10, 29; 5/4/10; 

5:15pm-9:23pm

4E+06

3 Feed Rate 460.7 kpph EPA Methods 

5,10, 29; 5/4/10; 

5:15pm-9:23pm

450

Thursday, February 03, 2011 Page 11 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

APCD Run Data

4 Heat Input Million Btus/million BTU using O2 5855 EPA Methods 25, 

26A; 5/2/10; 

3:10pm-6:18pm

5200

4 Net Electric Output 592.1 MW EPA Methods 25, 

26A; 5/2/10; 

3:10pm-6:18pm

580

4 Gross Electric Output 632.2 MW EPA Methods 25, 

26A; 5/2/10; 

3:10pm-6:18pm

610

4 Steam Output 5E+06 lbs/hr EPA Methods 25, 

26A; 5/2/10; 

3:10pm-6:18pm

4E+06

4 Feed Rate 460.8 kpph EPA Methods 25, 

26A; 5/2/10; 

3:10pm-6:18pm

450

5 Heat Input Million Btus/million BTU using O2 5834 EPA Methods 25, 

26A; 5/3/10; 

9:05am-12:18pm

5200

5 Net Electric Output 587.1 MW EPA Methods 25, 

26A; 5/3/10; 

9:05am-12:18pm

580

5 Gross Electric Output 627.8 MW EPA Methods 25, 

26A; 5/3/10; 

9:05am-12:18pm

610

5 Steam Output 5E+06 lbs/hr EPA Methods 25, 

26A; 5/3/10; 

9:05am-12:18pm

4E+06

5 Feed Rate 459.2 kpph EPA Methods 25, 

26A; 5/3/10; 

9:05am-12:18pm

450

6 Heat Input Million Btus/million BTU using O2 5833 EPA Methods 25, 

26A; 5/3/10; 

1:10pm-4:16pm

5200

6 Net Electric Output 586.3 MW EPA Methods 25, 

26A; 5/3/10; 

1:10pm-4:16pm

580

6 Gross Electric Output 627.1 MW EPA Methods 25, 

26A; 5/3/10; 

1:10pm-4:16pm

610

6 Steam Output 4E+06 lbs/hr EPA Methods 25, 

26A; 5/3/10; 

1:10pm-4:16pm

4E+06

6 Feed Rate 459.1 kpph EPA Methods 25, 

26A; 5/3/10; 

1:10pm-4:16pm

450

Target

Value

Thursday, February 03, 2011 Page 12 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 ELECTROSTATIC PRECIPITATOR 0 0

1 FGD wet limestone scrubber 0 0

1 SELECTIVE NONCATALYTIC REDUCTION 

FOR NOX

0 0

Run Name Value UOM Comments

1 TSS 0 mg/l

1 TDS 0 mg/l

1 Higher heating value 0 Btu/hr

1 moisture 0 %

1 Mercury 0 ppm

1 Selected Metals 0 ppm

1 chlorine 0 ppm

1 fluorine 0 ppm

Thursday, February 03, 2011 Page 13 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Sampling / Stack Data Results Detail

Location stack exhaust - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 03, 2011 Page 14 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Location stack exhaust - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Thursday, February 03, 2011 Page 15 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Location stack exhaust - Method 26A

Average

Run Number 1 2 3

Test Date 5/2/2010 5/3/2010 5/3/2010

Run Start Time 3:10:00 PM 9:05:00 AM 1:10:00 PM

Run Finish Time 5:55:00 PM 11:50:00 AM 3:55:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 180 180 180

Nozzle Diameter, inches 0.15 0.15 0.15 0.150

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.999 0.999 0.999 0.999

Barometric Pressure, inches of Mercury 29.97 29.97 29.97 29.970

Average Orifice Meter Differential, inches H2O 0.98 0.99 0.96 0.977

Dry Gas Meter Volume Sampled, cubic feet 102.900 103.560 102.220 102.893

Average Dry Gas Meter Temperature, °F 104.42 99.17 104.42 102.670

Dry Gas Meter Volume Sampled, dscf 96.556 98.090 95.913 96.853

Total Moisture Liquid collected, g 329.6 341.1 333.3 334.667

Volume of Water Vapor, standard cubic feet 15.51 16.06 15.69 15.753

Moisture Content of Stack Gas, % 13.84 14.07 14.06 13.990

Moisture Saturation at Stack Gas Temperature, % 23.59 24.00 23.41 23.667

Dry Mole Fraction 0.8616 0.8593 0.8594 0.860

Carbon Dioxide, % 11.31 11.2 10.92 11.143

Oxygen, % 8.31 8.35 8.5 8.387

Carbon Monoxide & Nitrogen, % 80.38 80.45 80.58 80.470

Fuel Factor 1.11 1.12 1.14

Dry Molecular Weight, lb/lb-Mole 30.14 30.13 30.09 30.120

Wet Molecular weight, lb/lb-Mole 28.46 28.42 28.39 28.423

Flue Gas Static Pressure, inches of H2O -1 -1.1 -1.1 -1.067

Absolute Flue Gas Pressure, inches of Mercury 29.90 29.89 29.89 29.893

Average Stack Gas Temperature, °F 147.25 147.92 146.92 147.363

Average Velocity Head, inches of H2O 2.4823502219

1334

2.540913377

80301

2.458001312

0453

2.494

Average Stack Gas Velocity, feet/second 95.58 96.84 95.22 95.880

Stack Cross-Sectional Area, square feet 380.133 380.133 380.133 380.133

Dry Volumetric Flow Rate, dry scfm 1,632,057.8 1,646,790.0 1,622,098.2 1,633,648.6

67

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,179,986.7 2,208,724.8 2,171,775.9 2,186,829.1

33

Percent Isokinetic of Sampling Rate, % 101.8 102.5 101.8 102.033

Percent Excess Air, % 64.4 64.8 66.5 65.233

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 264 264 264

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Thursday, February 03, 2011 Page 16 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Location stack exhaust - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 17 of 18
Santee Cooper - Cross Unit #1, ICR Section 114 Testing

Location stack exhaust - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Thursday, February 03, 2011 Page 18 of 18