Name: Tim Mordhorst

Title:

Company: Black Hills Corporation

Sign Date:

Name: Karl Breuer

Title: Senior Technical Writer

Company: Air Pollution Testing, Inc.

Sign Date: 8/24/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Neil Simpson II ICR Testing 2010

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, January 21, 2011 Page 1 of 27
Neil Simpson II ICR Testing 2010

Facility Information:

Neil Simpson II

13151 Highway 51

Gillette W 82718

Contact: Tim Mordhorst

Phone: 605-721-2181

Fax:

Email: Tim.Mordhorst@blackhillscorp.co

m

Testing Company:

Air Pollution Testing, Inc.

5530 Marshall Street

Arvada CO 80002

Contact: Scott Bouchard

Phone: 303-420-5949

Fax: 303-420-5920

Email: sbouchard@airtest.net

Air Permit Number:

3-2-158

Permitted Source ID/Name:

2 Neil Simpson II

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Plant constructed in 1995, wall fired pulverized coal boiler with low nox burners, dry hydrated lime fed scrubber and 

an electrostatic precipitator.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: Enter ARS ID FRS #: Enter FRS ID

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 111.25 0 0 0 1740 1260 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Chloride Method 26 3 60 0

Stack Exit Hydrogen Fluoride Method 26 3 60 0

Stack Exit Filterable Particulate Method 29 3 240 0

Regulation Description Compound Limit Unit

None 0

Friday, January 21, 2011 Page 2 of 27
Neil Simpson II ICR Testing 2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Method 5 was performed as an alternative to OTM-27 due to the small diameter of the sampling ports. The OTM-27 

sampling aparatus would not fit in the sampling port.

Run 1 Method 29 sampling times as entered indicate sampling only on June 22nd. Run 1 sampling was conducted on 

June 22nd and 23rd, but the ERT would not accept the data entered on two dates. Data was entered with some 

incorrect times to get around this apparent glitch in ERT. Please see attached sampling data sheets for the correct 

Method 29, Run 1 sampling times.

Stack Exit Antimony Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit O2 Method 3A O2 10 120 0

Stack Exit Co2 Method 3A CO2 10 120 0

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Friday, January 21, 2011 Page 3 of 27
Neil Simpson II ICR Testing 2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 10

Average

Run Number 1 2 3

Test Date 6/29/2010 6/29/2010 6/29/2010

Run Start Time 6:45:00 AM 9:46:00 

AM

12:39:00 PM

Run Finish Time 8:45:00 AM 11:46:00 

AM

2:39:00 PM

Carbon Dioxide, % 14.9 15 14.9 14.933

Oxygen, % 4.6 4.3 4.6 4.500

Dry Volumetric Flow Rate, dry scfm 213421 222021 227060 220,834.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 16 13.3 15.833

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Stack Exit - Method 25A

Average

Run Number 1 2 3

Test Date 6/29/2010 6/29/2010 6/29/2010

Run Start Time 6:45:00 AM 9:46:00 

AM

12:39:00 PM

Run Finish Time 8:45:00 AM 11:46:00 

AM

2:39:00 PM

Carbon Dioxide, % 14.9 15 14.9 14.933

Oxygen, % 4.6 4.3 4.3 4.400

Dry Volumetric Flow Rate, dry scfm 213421 222021 227060 220,834.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 16 13.3 15.833

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 4 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 26

Average

Run Number 1 2 3

Test Date 6/23/2010 6/23/2010 6/23/2010

Run Start Time 6:25:00 AM 11:35:00 

AM

4:36:00 PM

Run Finish Time 7:20:00 AM 12:30:00 

PM

5:31:00 PM

Net Run Time, minutes 60 60 60

Dry Gas Meter Volume Sampled, dscf 1.820 1.783 1.779 1.794

Moisture Content of Stack Gas, % 18.02 18.32 17.60 17.980

Moisture Saturation at Stack Gas Temperature, % 64.19 67.67 73.92 68.593

Carbon Dioxide, % 14 15.1 15.1 14.733

Oxygen, % 4.8 4.8 4.8 4.800

Average Stack Gas Temperature, °F 183.42 185.83 189.92 186.390

Dry Volumetric Flow Rate, dry scfm 221,566.9 223,617.6 221,915.3 222,366.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 384,327.3 390,767.2 386,838.4 387,310.967

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 5 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 6/22/2010 6/23/2010 6/23/2010

Run Start Time 1:47:00 PM 9:29:00 

AM

2:28:00 PM

Run Finish Time 6:10:00 PM 1:28:00 PM 6:55:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 158.087 155.360 156.711 156.719

Moisture Content of Stack Gas, % 18.21 18.08 17.57 17.953

Moisture Saturation at Stack Gas Temperature, % 64.48 67.67 73.92 68.690

Carbon Dioxide, % 14.4 15.1 15.1 14.867

Oxygen, % 4.8 4.8 4.8 4.800

Average Stack Gas Temperature, °F 183.25 185.83 189.92 186.333

Dry Volumetric Flow Rate, dry scfm 220,063.5 224,158.4 221,996.1 222,072.667

Actual Wet Volumetric Flue Gas Flow Rate, acfm 385,663.9 390,564.6 386,838.4 387,688.967

Percent Isokinetic of Sampling Rate, % 97.4 94.0 95.7 95.700

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Stack Exit - Method 3A CO2

Average

Run Number 1 10 2

Test Date 6/22/2010 6/29/2010 6/22/2010

Run Start Time 1:50:00 PM 12:39:00 

PM

3:58:00 PM

Run Finish Time 3:50:00 PM 2:39:00 PM 4:56:00 PM

Carbon Dioxide, % 14.4 14.9 15.1 14.800

Oxygen, % 4.9 4.3 4.8 4.667

Dry Volumetric Flow Rate, dry scfm 220060 227060 220060 222,393.333

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 13.3 18.2 16.567

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 6 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A CO2 3

Average

Run Number 3 4 5

Test Date 6/23/2010 6/23/2010 6/23/2010

Run Start Time 6:34:00 AM 8:52:00 

AM

11:19:00 AM

Run Finish Time 8:34:00 AM 10:52:00 

AM

1:18:00 PM

Carbon Dioxide, % 14 15.1 15.1 14.733

Oxygen, % 4.8 4.8 4.8 4.800

Dry Volumetric Flow Rate, dry scfm 224094 224094 224094 224,094.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.1 18.1 18.1 18.100

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Stack Exit - Method 3A CO2 3 6

Average

Run Number 6 7 8

Test Date 6/23/2010 6/23/2010 6/29/2010

Run Start Time 1:31:00 PM 3:37:00 PM 6:45:00 AM

Run Finish Time 3:31:00 PM 5:37:00 PM 8:45:00 AM

Carbon Dioxide, % 15 15.1 14.9 15.000

Oxygen, % 4.9 4.8 4.6 4.767

Dry Volumetric Flow Rate, dry scfm 221914 221914 213421 219,083.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 17.6 17.6 18.2 17.800

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 7 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A CO2 3 6 9

Average

Run Number 9

Test Date 6/29/2010

Run Start Time 9:46:00 AM

Run Finish Time 11:46:00 AM

Carbon Dioxide, % 15 15.000

Oxygen, % 4.3 4.300

Dry Volumetric Flow Rate, dry scfm 222021 222,021.000

F-Factor, dscfm/MMBtu @ %O2 9820 9,820.000

Moisture, % 16 16.000

Fuel Type Override

Fw 0 0.000

Fc 0 0.000

Location Stack Exit - Method 3A O2

Average

Run Number 1 10 2

Test Date 6/22/2010 6/29/2010 6/22/2010

Run Start Time 1:50:00 PM 12:39:00 

PM

3:58:00 PM

Run Finish Time 3:50:00 PM 2:39:00 PM 4:56:00 PM

Carbon Dioxide, % 14.4 14.9 15.1 14.800

Oxygen, % 4.9 4.3 4.8 4.667

Dry Volumetric Flow Rate, dry scfm 220060 227060 220060 222,393.333

F-Factor, dscfm/MMBtu @ %O2 9820 9820 0 6,546.667

Moisture, % 18.2 13.3 18.2 16.567

Fuel Type Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 8 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A O2 3

Average

Run Number 3 4 5

Test Date 6/23/2010 6/23/2010 6/23/2010

Run Start Time 6:34:00 AM 8:52:00 

AM

11:19:00 AM

Run Finish Time 8:34:00 AM 10:52:00 

AM

1:18:00 PM

Carbon Dioxide, % 14 15.1 15.1 14.733

Oxygen, % 4.8 4.8 4.8 4.800

Dry Volumetric Flow Rate, dry scfm 220060 224094 224094 222,749.333

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 18.1 18.1 18.133

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Location Stack Exit - Method 3A O2 3 6

Average

Run Number 6 7 8

Test Date 6/23/2010 6/23/2010 6/29/2010

Run Start Time 1:31:00 PM 3:37:00 PM 6:45:00 AM

Run Finish Time 3:31:00 PM 5:37:00 PM 8:45:00 AM

Carbon Dioxide, % 15 15.1 14.9 15.000

Oxygen, % 4.9 4.8 4.6 4.767

Dry Volumetric Flow Rate, dry scfm 221914 221914 213421 219,083.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 17.6 17.6 18.2 17.800

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 9 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A O2 3 6 9

Average

Run Number 9

Test Date 6/29/2010

Run Start Time 9:46:00 AM

Run Finish Time 11:46:00 AM

Carbon Dioxide, % 15 15.000

Oxygen, % 4.3 4.300

Dry Volumetric Flow Rate, dry scfm 222021 222,021.000

F-Factor, dscfm/MMBtu @ %O2 9820 9,820.000

Moisture, % 16 16.000

Fuel Type Override

Fw 0 0.000

Fc 0 0.000

Location Stack Exit - Method 5/OTM-28

Average

Run Number 1 2 3

Test Date 6/22/2010 6/23/2010 6/23/2010

Run Start Time 2:10:00 PM 9:29:00 

AM

2:28:00 PM

Run Finish Time 6:55:00 PM 12:59:00 

PM

6:55:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 156.897 158.166 154.050 156.371

Moisture Content of Stack Gas, % 14.28 16.98 14.84 15.367

Moisture Saturation at Stack Gas Temperature, % 70.36 67.92 72.99 70.423

Carbon Dioxide, % 14.4 15.1 15.1 14.867

Oxygen, % 4.8 4.8 4.8 4.800

Average Stack Gas Temperature, °F 187.25 186.00 189.33 187.527

Dry Volumetric Flow Rate, dry scfm 211,567.5 210,033.6 210,785.6 210,795.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 355,975.6 361,200.4 355,206.0 357,460.667

Percent Isokinetic of Sampling Rate, % 100.6 102.1 99.1 100.600

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 10 of 27
Neil Simpson II ICR Testing 2010

Emissions Summary

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 8.85E-02 1.40E-01 9.29E-02 0.107

ppm 9.67E+01 1.56E+02 1.01E+02 117.900

ppm@7%O2 8.25E+01 1.31E+02 8.61E+01 99.867

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 0.00E+00 2.10E-04 2.13E-04 0.000

ppm 0.00E+00 1.49E-01 1.51E-01 0.100

ppm@7%O2 0.00E+00 1.25E-01 1.26E-01 0.084

Location: Stack Exit - Method 26

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 0.00828 0.0106 0.00934 0.009

lb/mmBtuO2 1.28E-04 1.67E-04 1.48E-04 0.000

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.0207 0.0266 0.0234 0.024

lb/mmBtuO2 3.20E-04 4.19E-04 3.70E-04 0.000

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 2 3 1

Mass_mg 0.0001 0.000102 0.000129 0.000

Elb/hr 1.91E-05 1.91E-05 2.38E-05 0.000

lb/mmBtuO2 1.81E-08 1.83E-08 2.29E-08 0.000

mg/dscm 2.27E-05 2.30E-05 2.88E-05 0.000

mg/dscm@7%O2 1.96E-05 1.99E-05 2.49E-05 0.000

Compound: Arsenic

Average

RunNumber 2 3 1

Mass_mg 0.00015 0.000195 0.000215 0.000

Elb/hr 2.86E-05 3.65E-05 3.96E-05 0.000

lb/mmBtuO2 2.71E-08 3.50E-08 3.82E-08 0.000

mg/dscm 3.41E-05 4.39E-05 4.80E-05 0.000

mg/dscm@7%O2 2.94E-05 3.79E-05 4.14E-05 0.000

Compound: Beryllium

Average

Friday, January 21, 2011 Page 11 of 27
Neil Simpson II ICR Testing 2010

RunNumber 2 3 1

Mass_mg 0.000024 0.00003 0.000034 0.000

Elb/hr 4.58E-06 5.62E-06 6.26E-06 0.000

lb/mmBtuO2 4.34E-09 5.38E-09 6.04E-09 0.000

mg/dscm 5.46E-06 6.76E-06 7.60E-06 0.000

mg/dscm@7%O2 4.71E-06 5.84E-06 6.56E-06 0.000

Compound: Cadmium

Average

RunNumber 2 3 1

Mass_mg 0.000165 0.000263 0.00047 0.000

Elb/hr 3.15E-05 4.93E-05 8.65E-05 0.000

lb/mmBtuO2 2.98E-08 4.72E-08 8.36E-08 0.000

mg/dscm 3.75E-05 5.93E-05 1.05E-04 0.000

mg/dscm@7%O2 3.24E-05 5.12E-05 9.07E-05 0.000

Compound: Chromium

Average

RunNumber 2 3 1

Mass_mg 0.00232 0.00375 0.00427 0.003

Elb/hr 4.43E-04 7.03E-04 7.86E-04 0.001

lb/mmBtuO2 4.20E-07 6.73E-07 7.59E-07 0.000

mg/dscm 5.27E-04 8.45E-04 9.54E-04 0.001

mg/dscm@7%O2 4.55E-04 7.30E-04 8.24E-04 0.001

Compound: Filterable Particulate

Average

RunNumber 2 3 1

Mass_mg 3 1.8 5.6 3.467

Elb/hr 5.73E-01 3.37E-01 1.03E+00 0.647

lb/mmBtuO2 5.43E-04 3.23E-04 9.96E-04 0.001

mg/dscm 6.82E-01 4.06E-01 1.25E+00 0.779

mg/dscm@7%O2 5.89E-01 3.51E-01 1.08E+00 0.673

Compound: Lead

Average

RunNumber 2 3 1

Mass_mg 0.00096 0.00126 0.00331 0.002

Elb/hr 1.83E-04 2.36E-04 6.09E-04 0.000

lb/mmBtuO2 1.74E-07 2.26E-07 5.88E-07 0.000

mg/dscm 2.18E-04 2.84E-04 7.40E-04 0.000

mg/dscm@7%O2 1.88E-04 2.45E-04 6.39E-04 0.000

Compound: Manganese

Average

RunNumber 2 3 1

Mass_mg 0.00255 0.00365 0.00602 0.004

Elb/hr 4.87E-04 6.84E-04 1.11E-03 0.001

lb/mmBtuO2 4.61E-07 6.55E-07 1.07E-06 0.000

mg/dscm 5.80E-04 8.23E-04 1.34E-03 0.001

mg/dscm@7%O2 5.01E-04 7.11E-04 1.16E-03 0.001

Compound: Nickel

Average

Friday, January 21, 2011 Page 12 of 27
Neil Simpson II ICR Testing 2010

Process Run Data

RunNumber 2 3 1

Mass_mg 0.00346 0.00408 0.00598 0.005

Elb/hr 6.60E-04 7.65E-04 1.10E-03 0.001

lb/mmBtuO2 6.26E-07 7.32E-07 1.06E-06 0.000

mg/dscm 7.87E-04 9.20E-04 1.34E-03 0.001

mg/dscm@7%O2 6.79E-04 7.94E-04 1.16E-03 0.001

Compound: Selenium

Average

RunNumber 2 3 1

Mass_mg 0.00052 0.00052 0.00052 0.001

Elb/hr 9.92E-05 9.74E-05 9.58E-05 0.000

lb/mmBtuO2 9.41E-08 9.33E-08 9.24E-08 0.000

mg/dscm 1.18E-04 1.17E-04 1.16E-04 0.000

mg/dscm@7%O2 1.02E-04 1.01E-04 1.00E-04 0.000

Location: Stack Exit - Method 5/OTM-28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 9.65 4.45 6.45 6.850

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 78.6 48.8 28.5 51.967

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 5.2 3.1 3.7 4.000

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 93.45 563.5 38.65 231.867

Friday, January 21, 2011 Page 13 of 27
Neil Simpson II ICR Testing 2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 LOW NOX BURNERS 0 0

1 DRY SCRUBBER 0 0

1 ELECTROSTATIC PRECIPITATOR 0 0

Friday, January 21, 2011 Page 14 of 27
Neil Simpson II ICR Testing 2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 10

Average

Run Number 1 2 3

Test Date 6/29/2010 6/29/2010 6/29/2010

Run Start Time 6:45:00 AM 9:46:00 AM 12:39:00 PM

Run Finish Time 8:45:00 AM 11:46:00 AM 2:39:00 PM

Carbon Dioxide, % 14.9 15 14.9 14.933

Oxygen, % 4.6 4.3 4.6 4.500

Fuel Factor 1.09 1.11 1.09

Dry Volumetric Flow Rate, dry scfm 213421 222021 227060 220,834.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 16 13.3 15.833

Analyzer Make TECO TECO TECO

Analyzer Model 48C 48C 48C

Analyzer Serial Number 48-21571-198 48-21571-

198

48-21571-198

Operating Range 182 182 182 182.000

Operating Units ppm ppm ppm

No. Readings/Avg. 6 6 6 6.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0 0.1 0.033

Calibration Pre Zero Cylinder Bias 0 0 0.05 0.017

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM059451 ALM059451 ALM059451

Calibration Pre High Cylinder Instrument Response 78.8 77.6 78.2 78.200

Calibration Pre High Cylinder Bias 0.16 -0.49 -0.16 -0.163

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0.1 0.1 0.067

Calibration Post Zero Cylinder Bias 0 0.05 0.05 0.033

Calibration Post Zero Cylinder Drift 0 0.05 0 0.017

Calibration Post High Cylinder ID ALM059451 ALM059451 ALM059451

Calibration Post High Cylinder Instrument Response 77.6 78.2 78.2 78.000

Calibration Post High Cylinder Bias -0.49 -0.16 -0.16 -0.270

Calibration Post High Cylinder Drift 0.65 0.33 0 0.327

Cavg 96.8 155.1 101.6 117.833

Cavg Units ppmvd ppmvd ppmvd

Cgas 96.6762 155.5479 101.5 117.908

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 15 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 25A

Average

Run Number 1 2 3

Test Date 6/29/2010 6/29/2010 6/29/2010

Run Start Time 6:45:00 AM 9:46:00 AM 12:39:00 PM

Run Finish Time 8:45:00 AM 11:46:00 AM 2:39:00 PM

Carbon Dioxide, % 14.9 15 14.9 14.933

Oxygen, % 4.6 4.3 4.3 4.400

Fuel Factor 1.09 1.11 1.11

Dry Volumetric Flow Rate, dry scfm 213421 222021 227060 220,834.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 16 13.3 15.833

Analyzer Make TECO TECO TECO

Analyzer Model 55C 55C 55C

Analyzer Serial Number 55C-70304-

365

55C-70304-

365

55C-70304-

365

Operating Range 100 100 100 100.000

Operating Units ppm ppm ppm

No. Readings/Avg. 6 6 6 6.000

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 -0.1 0.2 0.033

Calibration Pre Zero Cylinder Bias 0 -0.05 0.11 0.020

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM010005 ALM010005 ALM010005

Calibration Pre High Cylinder Instrument Response 30 31 30.1 30.367

Calibration Pre High Cylinder Bias -0.1 -26.1 0 -8.733

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response -0.1 0.2 0.1 0.067

Calibration Post Zero Cylinder Bias -0.05 0.11 0.05 0.037

Calibration Post Zero Cylinder Drift 0.05 0.16 0.06 0.090

Calibration Post High Cylinder ID ALM010005 ALM010005 ALM010005

Calibration Post High Cylinder Instrument Response 31 30.1 30.4 30.500

Calibration Post High Cylinder Bias 0.9 0 0.3 0.400

Calibration Post High Cylinder Drift 1 26.1 0.3 9.133

Cavg 0 0.2 0.3 0.167

Cavg Units ppmvd ppmvd ppmvd

Cgas 0 0.1485 0.1505 0.100

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 16 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 26

Average

Run Number 1 2 3

Test Date 6/23/2010 6/23/2010 6/23/2010

Run Start Time 6:25:00 AM 11:35:00 AM 4:36:00 PM

Run Finish Time 7:20:00 AM 12:30:00 PM 5:31:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 60 60 60

Nozzle Diameter, inches

Pitot Tube Coefficient 0.82 0.82 0.82 0.820

Dry Gas Meter Calibration Factor 1.001 1.001 1.001 1.001

Barometric Pressure, inches of Mercury 25.72 25.72 25.72 25.720

Average Orifice Meter Differential, inches H2O 0.00 0.00 0.00 0.000

Dry Gas Meter Volume Sampled, cubic feet 2.126 2.124 2.131 2.127

Average Dry Gas Meter Temperature, °F 70.79 81.21 84.38 78.793

Dry Gas Meter Volume Sampled, dscf 1.820 1.783 1.779 1.794

Total Moisture Liquid collected, g 8.4 8.5 8 8.300

Volume of Water Vapor, standard cubic feet 0.40 0.40 0.38 0.393

Moisture Content of Stack Gas, % 18.02 18.32 17.60 17.980

Moisture Saturation at Stack Gas Temperature, % 64.19 67.67 73.92 68.593

Dry Mole Fraction 0.8198 0.8168 0.824 0.820

Carbon Dioxide, % 14 15.1 15.1 14.733

Oxygen, % 4.8 4.8 4.8 4.800

Carbon Monoxide & Nitrogen, % 81.2 80.1 80.1 80.467

Fuel Factor 1.15 1.07 1.07

Dry Molecular Weight, lb/lb-Mole 30.43 30.61 30.61 30.550

Wet Molecular weight, lb/lb-Mole 28.19 28.30 28.39 28.293

Flue Gas Static Pressure, inches of H2O -1.1 -1.1 -1.1 -1.100

Absolute Flue Gas Pressure, inches of Mercury 25.64 25.64 25.64 25.640

Average Stack Gas Temperature, °F 183.42 185.83 189.92 186.390

Average Velocity Head, inches of H2O 2.0584521117

8737

2.128272241

98024

2.079202150

79163

2.089

Average Stack Gas Velocity, feet/second 94.89 96.48 95.51 95.627

Stack Cross-Sectional Area, square feet 67.504 67.504 67.504 67.504

Dry Volumetric Flow Rate, dry scfm 221,566.9 223,617.6 221,915.3 222,366.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 384,327.3 390,767.2 386,838.4 387,310.967

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, % 28.9 29.4 29.4 29.233

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Round Duct Diameter, inches 111.25 111.25 111.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 17 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 6/22/2010 6/23/2010 6/23/2010

Run Start Time 1:47:00 PM 9:29:00 AM 2:28:00 PM

Run Finish Time 6:10:00 PM 1:28:00 PM 6:55:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.195 0.195 0.195 0.195

Pitot Tube Coefficient 0.82 0.82 0.82 0.820

Dry Gas Meter Calibration Factor 0.996 0.996 0.996 0.996

Barometric Pressure, inches of Mercury 25.51 25.72 25.72 25.650

Average Orifice Meter Differential, inches H2O 1.75 1.78 1.81 1.780

Dry Gas Meter Volume Sampled, cubic feet 188.093 181.320 189.910 186.441

Average Dry Gas Meter Temperature, °F 76.17 70.29 90.67 79.043

Dry Gas Meter Volume Sampled, dscf 158.087 155.360 156.711 156.719

Total Moisture Liquid collected, g 747.6 728.6 709.7 728.633

Volume of Water Vapor, standard cubic feet 35.19 34.30 33.41 34.300

Moisture Content of Stack Gas, % 18.21 18.08 17.57 17.953

Moisture Saturation at Stack Gas Temperature, % 64.48 67.67 73.92 68.690

Dry Mole Fraction 0.8179 0.8192 0.8243 0.820

Carbon Dioxide, % 14.4 15.1 15.1 14.867

Oxygen, % 4.8 4.8 4.8 4.800

Carbon Monoxide & Nitrogen, % 80.8 80.1 80.1 80.333

Fuel Factor 1.12 1.07 1.07

Dry Molecular Weight, lb/lb-Mole 30.50 30.61 30.61 30.573

Wet Molecular weight, lb/lb-Mole 28.22 28.33 28.39 28.313

Flue Gas Static Pressure, inches of H2O -1.1 -1.1 -1.1 -1.100

Absolute Flue Gas Pressure, inches of Mercury 25.43 25.64 25.64 25.570

Average Stack Gas Temperature, °F 183.25 185.83 189.92 186.333

Average Velocity Head, inches of H2O 2.0584521117

8737

2.128272241

98024

2.079202150

79163

2.089

Average Stack Gas Velocity, feet/second 95.22 96.43 95.51 95.720

Stack Cross-Sectional Area, square feet 67.504 67.504 67.504 67.504

Dry Volumetric Flow Rate, dry scfm 220,063.5 224,158.4 221,996.1 222,072.667

Actual Wet Volumetric Flue Gas Flow Rate, acfm 385,663.9 390,564.6 386,838.4 387,688.967

Percent Isokinetic of Sampling Rate, % 97.4 94.0 95.7 95.700

Percent Excess Air, % 29.0 29.4 29.4 29.267

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Round Duct Diameter, inches 111.25 111.25 111.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 18 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A CO2

Average

Run Number 1 10 2

Test Date 6/22/2010 6/29/2010 6/22/2010

Run Start Time 1:50:00 PM 12:39:00 PM 3:58:00 PM

Run Finish Time 3:50:00 PM 2:39:00 PM 4:56:00 PM

Carbon Dioxide, % 14.4 14.9 15.1 14.800

Oxygen, % 4.9 4.3 4.8 4.667

Fuel Factor 1.11 1.11 1.07

Dry Volumetric Flow Rate, dry scfm 220060 227060 220060 222,393.333

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 13.3 18.2 16.567

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1420C 1420C 1420C

Analyzer Serial Number 1689 272 272 744.333

Operating Range 19.2 19.2 19.2 19.200

Operating Units % % %

No. Readings/Avg. 6 6 6 6.000

Calibration Set 3 4 3 3.333

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC-133191 (2) ALM024737

 (2)

CC-133191 

(2)

Calibration Pre High Cylinder Instrument Response 5.1 10.1 5.1 6.767

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID CC-133191 (2) ALM024737

 (2)

CC-133191 

(2)

Calibration Post High Cylinder Instrument Response 5.1 10.1 5.1 6.767

Calibration Post High Cylinder Bias 0 0 0 0.000

Calibration Post High Cylinder Drift 0 0 0 0.000

Cavg 14.5 14.9 15.1 14.833

Cavg Units %vd %vd %vd

Cgas 14.4431 14.9 15.0408 14.795

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 19 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A CO2 3

Average

Run Number 3 4 5

Test Date 6/23/2010 6/23/2010 6/23/2010

Run Start Time 6:34:00 AM 8:52:00 AM 11:19:00 AM

Run Finish Time 8:34:00 AM 10:52:00 AM 1:18:00 PM

Carbon Dioxide, % 14 15.1 15.1 14.733

Oxygen, % 4.8 4.8 4.8 4.800

Fuel Factor 1.15 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 224094 224094 224094 224,094.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.1 18.1 18.1 18.100

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1420C 1420C 1420C

Analyzer Serial Number 272 272 272 272.000

Operating Range 19.2 19.2 19.2 19.200

Operating Units % % %

No. Readings/Avg. 6 6 6 6.000

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC-133191 (2) CC-133191 

(2)

CC-133191 

(2)

Calibration Pre High Cylinder Instrument Response 5.1 5.1 5.1 5.100

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID CC-133191 (2) CC-133191 

(2)

CC-133191 

(2)

Calibration Post High Cylinder Instrument Response 5.1 5.1 5.1 5.100

Calibration Post High Cylinder Bias 0 0 0 0.000

Calibration Post High Cylinder Drift 0 0 0 0.000

Cavg 14.1 15.1 15.2 14.800

Cavg Units %vd %vd %vd

Cgas 14.0447 0 15.1404 9.728

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 20 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A CO2 3 6

Average

Run Number 6 7 8

Test Date 6/23/2010 6/23/2010 6/29/2010

Run Start Time 1:31:00 PM 3:37:00 PM 6:45:00 AM

Run Finish Time 3:31:00 PM 5:37:00 PM 8:45:00 AM

Carbon Dioxide, % 15 15.1 14.9 15.000

Oxygen, % 4.9 4.8 4.6 4.767

Fuel Factor 1.07 1.07 1.09

Dry Volumetric Flow Rate, dry scfm 221914 221914 213421 219,083.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 17.6 17.6 18.2 17.800

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1420C 1420C 1420C

Analyzer Serial Number 272 272 272 272.000

Operating Range 19.2 19.2 19.2 19.200

Operating Units % % %

No. Readings/Avg. 6 6 6 6.000

Calibration Set 3 3 4 3.333

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC-133191 (2) CC-133191 

(2)

ALM024737 

(2)

Calibration Pre High Cylinder Instrument Response 5.1 5.1 10.1 6.767

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID CC-133191 (2) CC-133191 

(2)

ALM024737 

(2)

Calibration Post High Cylinder Instrument Response 5.1 5.1 10.1 6.767

Calibration Post High Cylinder Bias 0 0 0 0.000

Calibration Post High Cylinder Drift 0 0 0 0.000

Cavg 15.1 15.2 14.9 15.067

Cavg Units %vd %vd %vd

Cgas 15.0408 15.1404 14.9 15.027

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 21 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A CO2 3 6 9

Average

Run Number 9

Test Date 6/29/2010

Run Start Time 9:46:00 AM

Run Finish Time 11:46:00 AM

Carbon Dioxide, % 15 15.000

Oxygen, % 4.3 4.300

Fuel Factor 1.11

Dry Volumetric Flow Rate, dry scfm 222021 222,021.000

F-Factor, dscfm/MMBtu @ %O2 9820 9,820.000

Moisture, % 16 16.000

Analyzer Make Servomex

Analyzer Model 1420C

Analyzer Serial Number 272 272.000

Operating Range 19.2 19.200

Operating Units %

No. Readings/Avg. 6 6.000

Calibration Set 4 4.000

Calibration Pre Zero Cylinder ID CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0.000

Calibration Pre Zero Cylinder Bias 0 0.000

Calibration Pre Zero Cylinder Drift 0 0.000

Calibration Pre High Cylinder ID ALM024737 

(2)

Calibration Pre High Cylinder Instrument Response 10.1 10.100

Calibration Pre High Cylinder Bias 0 0.000

Calibration Pre High Cylinder Drift 0 0.000

Calibration Post Zero Cylinder ID CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0.000

Calibration Post Zero Cylinder Bias 0 0.000

Calibration Post Zero Cylinder Drift 0 0.000

Calibration Post High Cylinder ID ALM024737 

(2)

Calibration Post High Cylinder Instrument Response 10.1 10.100

Calibration Post High Cylinder Bias 0 0.000

Calibration Post High Cylinder Drift 0 0.000

Cavg 15 15.000

Cavg Units %vd

Cgas 15 15.000

Cgas Units %vd

Fuel Type Override

Fw 0 0.000

Fc 0 0.000

Cgasw 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 22 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A O2

Average

Run Number 1 10 2

Test Date 6/22/2010 6/29/2010 6/22/2010

Run Start Time 1:50:00 PM 12:39:00 PM 3:58:00 PM

Run Finish Time 3:50:00 PM 2:39:00 PM 4:56:00 PM

Carbon Dioxide, % 14.4 14.9 15.1 14.800

Oxygen, % 4.9 4.3 4.8 4.667

Fuel Factor 1.11 1.11 1.07

Dry Volumetric Flow Rate, dry scfm 220060 227060 220060 222,393.333

F-Factor, dscfm/MMBtu @ %O2 9820 9820 0 6,546.667

Moisture, % 18.2 13.3 18.2 16.567

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1420C 1420C 1420C

Analyzer Serial Number 1689 1689 1689 1,689.000

Operating Range 20.9 20.9 20.9 20.900

Operating Units % % %

No. Readings/Avg. 6 6 6 6.000

Calibration Set 5 6 5 5.333

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC-133191(1) ALM024737

 (1)

CC133191(1)

Calibration Pre High Cylinder Instrument Response 5 10.1 5.1 6.733

Calibration Pre High Cylinder Bias -40.38 0 0.48 -13.300

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID CC-133191(1) ALM024737

 (1)

CC133191(1)

Calibration Post High Cylinder Instrument Response 5.1 10.1 5 6.733

Calibration Post High Cylinder Bias -40.33 0 0 -13.443

Calibration Post High Cylinder Drift 5.0000000000

0043E-02

0 0.48 0.177

Cavg 4.9 4.3 4.8 4.667

Cavg Units %vd %vd %vd

Cgas 75.7802 4.3 4.762 28.281

Cgas Units %vd %vd %vd

Fuel Type Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 23 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A O2 3

Average

Run Number 3 4 5

Test Date 6/23/2010 6/23/2010 6/23/2010

Run Start Time 6:34:00 AM 8:52:00 AM 11:19:00 AM

Run Finish Time 8:34:00 AM 10:52:00 AM 1:18:00 PM

Carbon Dioxide, % 14 15.1 15.1 14.733

Oxygen, % 4.8 4.8 4.8 4.800

Fuel Factor 1.15 1.07 1.07

Dry Volumetric Flow Rate, dry scfm 220060 224094 224094 222,749.333

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 18.2 18.1 18.1 18.133

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1420C 1420C 1420C

Analyzer Serial Number 1689 1689 1689 1,689.000

Operating Range 20.9 20.9 20.9 20.900

Operating Units % % %

No. Readings/Avg. 6 6 6 6.000

Calibration Set 5 5 5 5.000

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC-133191(1) CC133191(1)CC133191(1)

Calibration Pre High Cylinder Instrument Response 5 5 5 5.000

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID CC-133191(1) CC133191(1)CC133191(1)

Calibration Post High Cylinder Instrument Response 5 5 5 5.000

Calibration Post High Cylinder Bias 0 0 0 0.000

Calibration Post High Cylinder Drift 0 0 0 0.000

Cavg 4.8 4.8 4.8 4.800

Cavg Units %vd %vd %vd

Cgas 4.8096 4.8096 4.8096 4.810

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 24 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A O2 3 6

Average

Run Number 6 7 8

Test Date 6/23/2010 6/23/2010 6/29/2010

Run Start Time 1:31:00 PM 3:37:00 PM 6:45:00 AM

Run Finish Time 3:31:00 PM 5:37:00 PM 8:45:00 AM

Carbon Dioxide, % 15 15.1 14.9 15.000

Oxygen, % 4.9 4.8 4.6 4.767

Fuel Factor 1.07 1.07 1.09

Dry Volumetric Flow Rate, dry scfm 221914 221914 213421 219,083.000

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Moisture, % 17.6 17.6 18.2 17.800

Analyzer Make Servomex Servomex Servomex

Analyzer Model 1420C 1420C 1420C

Analyzer Serial Number 1689 1689 1689 1,689.000

Operating Range 20.9 20.9 20.9 20.900

Operating Units % % %

No. Readings/Avg. 6 6 6 6.000

Calibration Set 5 5 6 5.333

Calibration Pre Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID CC-133191(1) CC133191(1)ALM024737 

(1)

Calibration Pre High Cylinder Instrument Response 5 5 10.1 6.700

Calibration Pre High Cylinder Bias 0 0 0 0.000

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID CC-131138 CC-131138 CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0 0 0.000

Calibration Post Zero Cylinder Bias 0 0 0 0.000

Calibration Post Zero Cylinder Drift 0 0 0 0.000

Calibration Post High Cylinder ID CC-133191(1) CC133191(1)ALM024737 

(1)

Calibration Post High Cylinder Instrument Response 5 5 10.1 6.700

Calibration Post High Cylinder Bias 0 0 0 0.000

Calibration Post High Cylinder Drift 0 0 0 0.000

Cavg 4.9 4.8 4.6 4.767

Cavg Units %vd %vd %vd

Cgas 4.9098 4.8096 4.6 4.773

Cgas Units %vd %vd %vd

Fuel Type Override Override Override

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 25 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 3A O2 3 6 9

Average

Run Number 9

Test Date 6/29/2010

Run Start Time 9:46:00 AM

Run Finish Time 11:46:00 AM

Carbon Dioxide, % 15 15.000

Oxygen, % 4.3 4.300

Fuel Factor 1.11

Dry Volumetric Flow Rate, dry scfm 222021 222,021.000

F-Factor, dscfm/MMBtu @ %O2 9820 9,820.000

Moisture, % 16 16.000

Analyzer Make Servomex

Analyzer Model 1420C

Analyzer Serial Number 1689 1,689.000

Operating Range 20.9 20.900

Operating Units %

No. Readings/Avg. 6 6.000

Calibration Set 6 6.000

Calibration Pre Zero Cylinder ID CC-131138

Calibration Pre Zero Cylinder Instrument Response 0 0.000

Calibration Pre Zero Cylinder Bias 0 0.000

Calibration Pre Zero Cylinder Drift 0 0.000

Calibration Pre High Cylinder ID ALM024737 

(1)

Calibration Pre High Cylinder Instrument Response 10.1 10.100

Calibration Pre High Cylinder Bias 0 0.000

Calibration Pre High Cylinder Drift 0 0.000

Calibration Post Zero Cylinder ID CC-131138

Calibration Post Zero Cylinder Instrument Response 0 0.000

Calibration Post Zero Cylinder Bias 0 0.000

Calibration Post Zero Cylinder Drift 0 0.000

Calibration Post High Cylinder ID ALM024737 

(1)

Calibration Post High Cylinder Instrument Response 10.1 10.100

Calibration Post High Cylinder Bias 0 0.000

Calibration Post High Cylinder Drift 0 0.000

Cavg 4.3 4.300

Cavg Units %vd

Cgas 4.3 4.300

Cgas Units %vd

Fuel Type Override

Fw 0 0.000

Fc 0 0.000

Cgasw 0 0.000

Cgasw Units

Friday, January 21, 2011 Page 26 of 27
Neil Simpson II ICR Testing 2010

Location Stack Exit - Method 5/OTM-28

Average

Run Number 1 2 3

Test Date 6/22/2010 6/23/2010 6/23/2010

Run Start Time 2:10:00 PM 9:29:00 AM 2:28:00 PM

Run Finish Time 6:55:00 PM 12:59:00 PM 6:55:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.195 0.195 0.195 0.195

Pitot Tube Coefficient 0.83 0.83 0.83 0.830

Dry Gas Meter Calibration Factor 0.997 0.997 0.997 0.997

Barometric Pressure, inches of Mercury 25.51 25.72 25.72 25.650

Average Orifice Meter Differential, inches H2O 1.61 1.65 1.65 1.637

Dry Gas Meter Volume Sampled, cubic feet 184.404 184.405 186.583 185.131

Average Dry Gas Meter Temperature, °F 69.96 70.08 90.67 76.903

Dry Gas Meter Volume Sampled, dscf 156.897 158.166 154.050 156.371

Total Moisture Liquid collected, g 555.4 687.4 570.5 604.433

Volume of Water Vapor, standard cubic feet 26.14 32.36 26.85 28.450

Moisture Content of Stack Gas, % 14.28 16.98 14.84 15.367

Moisture Saturation at Stack Gas Temperature, % 70.36 67.92 72.99 70.423

Dry Mole Fraction 0.8572 0.8302 0.8516 0.846

Carbon Dioxide, % 14.4 15.1 15.1 14.867

Oxygen, % 4.8 4.8 4.8 4.800

Carbon Monoxide & Nitrogen, % 80.8 80.1 80.1 80.333

Fuel Factor 1.12 1.07 1.07

Dry Molecular Weight, lb/lb-Mole 30.50 30.61 30.61 30.573

Wet Molecular weight, lb/lb-Mole 28.72 28.47 28.74 28.643

Flue Gas Static Pressure, inches of H2O -1.1 -1.1 -1.1 -1.100

Absolute Flue Gas Pressure, inches of Mercury 25.43 25.64 25.64 25.570

Average Stack Gas Temperature, °F 187.25 186.00 189.33 187.527

Average Velocity Head, inches of H2O 1.7311628596

1299

1.784817946

70104

1.733750379

1294

1.750

Average Stack Gas Velocity, feet/second 87.89 89.18 87.70 88.257

Stack Cross-Sectional Area, square feet 67.504 67.504 67.504 67.504

Dry Volumetric Flow Rate, dry scfm 211,567.5 210,033.6 210,785.6 210,795.567

Actual Wet Volumetric Flue Gas Flow Rate, acfm 355,975.6 361,200.4 355,206.0 357,460.667

Percent Isokinetic of Sampling Rate, % 100.6 102.1 99.1 100.600

Percent Excess Air, % 29.0 29.4 29.4 29.267

F-Factor, dscfm/MMBtu @ %O2 9820 9820 9820 9,820.000

Round Duct Diameter, inches 111.25 111.25 111.25

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Friday, January 21, 2011 Page 27 of 27