May 8, 2007 

Robert Weisner 

WPCD 

26th & Main Streets 

P.O. Box 6348 

226 Rankin Road, Washington, PA 15301 

phone: 304-233-1783 fax: 304-233-1785 

Wheeling, WV 26003-0800 

Subject: Letter dated 4/18/07 

Surcharging the metering Vault 

Dear Mr. Weisner: 

As per our several conversations concerning this matter, LAD has been exploring 

other ways of introducing our discharge into the municipal system. As we have all 

agreed, the existing route because of its awkward flow pattern has restricted our 

discharge simply by hydraulic head losses in the line. This was further exacerbated by 

EPS moving our sewer line to expand there building in 2001 and installing two 45-degree 

jogs in the line. These factors have caused the existing 8" line to become limited to only 

50% of its flow capacity. 

After receiving the City's sewer drawing on Friday 5/5/07, an exhausted review of 

the alternates was conducted. There appears to be two viable options as presented below. 

OPTION#1 

GRAVITY LINE TO INCEPTOR VIA RAILROAD PROPERTY AND SAFETY 

KLEEN 

This option would require approximately 900 feet of sewer line and possibly 

three (3) easements. Also, it would require the installation of a diversion box that would 

allow flow to both the existing sewer line and the direct line to the interceptor. 

OPTION#2 . 

PUMP STATION AND FORCE MAIN TO FIRST BLA W-KNOX SEWER ON 

PENINSULA STREET 

The manhole is an old Blaw-Knox sewer located in the sidewalk across the street 

about 400 feet from our metering pit. This appears accessible via our property and a 

public utility right-of-way. Therefore, NO easements would be required. This option 

obviously would require a pump station and automatic valving to transfer wastewater that 

prevents the metering pit from surcharging. 
Page 2 of2 

Although the drawings provided by the City do NOT show a Manhole at the 

comer closest to our building, it seems that one should exist in the Southwest comer of 

the old Blaw-Knox building. Could the City research this possibility? 

Based upon either option, LAD would be required to install a new receiving 

chamber immediately after the metering pit. Therefore, at this time, we would like to 

request postponing the installation of the "emergency spill" valve scheduled for 5/24/07 

until a decision is made concerning the routing of the discharge. LAD could then 

incorporate the valve into the new system. 

Also, is it correct to assume that the existing "old" Blaw-Knox sewer line is a 

good functioning sewer or should LAD camera the line to confirm that assumption? 

Please advise. 

Mr. Weisner, we would like to thank you for your assistance in this matter both 

from a discussion and informational standpoint and we will be contacting you within the 

next several weeks for additional information before we can select our preferred option. 

If you have any questions concerning this matter, please feel free to contact me. 

Cc: King Campbell, Plant Superintendent 

Chuck Neuhardt, PT Specialist 
11/05/2007 12:04 4123212283 lv!FG PGH PAGE 04/05 
lD 

c:;) 

......... 

lD ~ w 

CD 

<I 

ll.. 

COMMONWEALTH OF PENNSYLVANIA 

DEPARTMENT OF ENVIRONMENTAL PROTECT

OFFICE OF FIELD OPERAT/01\'S 

BUREAU OF LABORATORIES 

----

------

------------

------

~ 

CD ~ CD ~ L 

M 

co 

C'l 

C'l 

<"""i 

C'l 

[') 

C'l 

<"""i 

'<j" 

'<j" 

c:;) 

N 

<"""i 

1'"'-

c:;) ~ C'l 

........ 

Ln ~ ......... 

<"""i 

rl 

Certificate not b:allsfernble S11m:oder upon re\'ocation 

To Be ~n:>picuously Displayed at tbc Laborut.ory 

Z.:ol vaiid unle~s aceomp~¢ by: a \'alid Scope ofA~<'.reditation 

Sball not be used 10 imply endol1icmenl by the CollJI;IlooweRllh of Pei!JlS11vanil!. 

Cvstomcl'li are urged to verify die laiJora(l)ry's cuiwnt slaws 

z4~
December 22, 2008 

Mr. Chuck Neuhardt 

Pretreatment Coordinator 

Citl Of Wheeling - WPCD 

26t & Main Streets 

Wheeling, WV. 26003 

J jl 

TRA-DET INC. 

P.O. BOX 2019 

WHEEUNG, WV 26003~219 

(304) 547-9094 

FAX: (304) 547-9097 

SHIPPING ADDRESS 

2596 BATTLE RUN ROAD 

TRIADELPHIA, WV 26059-9609 

Subject: Ana1:y1ical Training: Chlor:d~ 1\naiysis by Ion Selective Electrode 

Dear Mr. Neuhardt: 

At the request of Liquid Assets Disposal, Tra-Det Laboratories provided training of Mr. 

Matthew A. Kicinski on the performance of chloride analysis using an ORION 4 STAR 

instrument with an Ion Selective Electrode (ISE) to measure daily chloride levels in the 

influent and effluent of the LAD treatment plant. I spent approximately one-hour calibrating 

the instrument against our in-house standards and once assured that the instrument was 

working properly, trained Mr. Kicinski how to use it. The training exercise took 

approximately two (2) hours until Mr. Kicinski became proficient with the instrument and 

skilled in calibrating it. 

The purpose of this letter is to document the Training exercise and advise the City that the 

analytical data produced using the ORION 4 Star instrument with the ISE probe should be 

creditable and accurate. The ORION 4 Star measures to 10 %accuracy, hence a reading of 

5000 mg/L would range from 4500 mg/L to 5500 mg/L with an additional 5 % error. 

If you have any questions concerning this TRAINING, please call me at 304-547-9094. 

Best regards, 

~~ Laboratory Manager, Tra-Det 
226 Rankin Road, Washington, PA 15301 

phone: 304-233-1783 fax: 304-233-1785 

December 15, 2008 

A.King Campbell 

Plant Superintendent 

ciz of Wheeling 

26 & Main Street 

P.O. Box 6348 

Wheeling, WV. 26003 

Subject: Request for Flow limit Continuation 

Dear Mr. King: 

As per our meeting of 12/10/08, LAD kindly request a continuation of the existing 

flow limitation of235,000 gallons per day until the permit expires on September 30, 

- 2009. (9 months). 

This request is based upon the substantial capital improvements installed in our 

plant in 2008. The capital treatment improvements included the installation of a new 

"state of the art" rotary press for more reliable solids removal and dewatering and a 

200,000 gallon equalization tank. In addition other metering instrumentation were 

installed to allow more operator awareness of operating equipment. 

As you and your staff indicated during the meeting, the wastewater plant at the City 

of Wheeling has been operating in full compliance with its NPDES permit for 3-4months 

along with the UV system and you attribute it to our improvements. 

Therefore, LAD kindly request we maintain the same flow rate until September 

2009 when it can again be discussed. Please advise of your decision as soon as possible 

since the flow rate reduction becomes effective 1/1/09. (2 weeks) 

Cc: Chuck Neuhardt, City of Wheeling 
226 Rankin Road, Washington, PA 15301 

phone: 304-233-1783 fax: 304-233-1785 

December 15,2008 

A.King Campbell 

Plant Superintendent 

Ci~ Of Wheeling 

26 & Main Street 

P.O. Box 6348 

Wheeling, WV. 26003 

.... L 

Subject: TREATMENT FOR CHLORIDES AND ANALTYICAL SCREENING 

Dear Mr. King: 

During our meeting of 12/10/08, I explained that LAD was implementing efforts to 

assess the concentration of chlorides entering our plant. We experienced problems with 

being able to be provided an instrument that functioned. After receiving two consecutive 

non-functional chloride analytical measuring units using a selective ion probe, the third 

unit appears to be operating. LAD is checking the results by a second method using a 

titration procedure. 

We are now testing every truck entering our plant and have placed a 10,000 mg/1 

chloride limit on incoming wastewaters from the oil and gas industry. We have been 

blending septage press water and other non-chloride waters with the production fluids in 

an attempt to meet the permit limits. 

Also, the purpose of this letter is to advise you that LAD will be conducting a full 

scale pilot plant testing operation for the removal of chlorides beginning the week of 

January 19,2009. The exact technology being employed will involve ultra-filtration, 

ozonation, and RO membranes. Treated water during this pilot study will be RECYCLED 

to the drilling fields for re-use. 

We will keep you advised of our progress. 

VP Engineering 

Cc; Chuck Neuhardt, City of Wheeling 
921 Saw Mill Run Blvd., Pittsburgh, PA 15220 

phone: 4121381-0459 fax: 4121381-6271 

September 16, 2008 

A. King Campbell 

WPCD Plant Superintendent 

26th & Main Street 

P.O. Box 6348 

Wheeling, WV 26003 

Subject: Progress Report 

Interim Permit Modification compliance Schedule 

Dear Mr. Campbell: 

SEP 18 20U8 

This is a follow-up progress report on our letter of March 25, 2008 whereby 

you were advised of our intentions to "reduce flow and improve wastewater quality" 

discharged to the City of Wheeling. LAD is pleased to report that we have 

accomplished all three (3) objectives of our proposed schedule. 

1. The FOURNIER Rotary Press has been installed three weeks ahead of 

schedule (10/7/08) and fully operational. Operator training and process 

troubleshooting were completed last week and the equipment is now being 

used daily to press ALL septage wastewater. The filtrate has successfully 

accomplished meeting suspended solids concentrations of less than 500 mg/1. 

You and your staff are welcome to visit the plant to inspect the operation and 

performance of the press. 

2. The 200,000 gallon equalization and pH adjustment treatment tank will be 

fully operational by Friday 9/19/08, a full month ahead of schedule. The tank 

is for eflluent flow limit compliance. 

Any wastewater above the current daily limit of235,000 gallons per day will 

be held and released when effluent allocations allow. 

3. LAD has been in compliance with the imposed discharge limit of235,000 gallons 

and has limited brine disposal to approximately 10,000 gallons per day at the plant. 

4. LAD remains in the BWQ sampling procedure as required by the WVDEP despite 

consistent analytical results of the stream water quality. A NPDES discharge permit 

possibilty does NOT appear optimistic based on the negative feedback received from 

the WVDEP. However LAD continues to pursue the matter. 

After review of this information if you have any questions or desire to schedule a visit at 

the plant to observe the press operation, please call John Marchinsky at 304-233-1783. 

Cc: ,_. .Chuck Neuhardt 

Dan Valanti 
'March 25,2008 

A King Campbell 

226 Rankin Road, Washington, PA 15301 

phone: 304-233-1783 fax: 304-233-1785 

-. WPCD Plant Superintendent 

26th & Main Streets 

P.O. Box 6348 

Wheeling, WV 26003 

Subject: LIQUID ASSETS DISPOSAL 

Interim Permit Modification Compliance Schedule for 

reducing flow and improving wastewater quality 

Meeting 3/18/08 

Dear Mr. Campbell: 

As per your request and the results of olir meeting notes recorded there from taken 

on 3/18/08, the purpose of this letter is to confmn as stated in the meeting that LAD has 

already begun to upgrade its treatment processes by ordering a NEW rotary type press 

manufactured by Fournier Industries of Canada. Several members of your staffwitnessed 

the latest demonstration test at our facility. At that time LAD was treating and testing 

every type of septage wastewater entering the plant for those two days. This testing event 

was the second and confirming demonstration. The results of these tests where very 

favorable and reconfirmed our initial results. Subsequently, LAD issued a Purchase 

Order for this equipment. Presented to you during the meeting of 3/18/08 was a copy of 

our PURCHASE ORDER and contract with Fournier ordering a six (6)-channel press. 

The delivery schedule for this equipment as outlined in the purchase order dated 3/11/08 

was 20 weeks. After delivery, about 6 weeks is required to remove the old press, install 

and make operational the new press. The earliest possible date of operation is anticipated 

to be about 10/7/08, if the anticipated schedule does NOT experience any delays. 

Simultaneous with this effort, LAD has also already begun two other related 

efforts: I) to petition WVDEP for an NPDES for the OIL and GAS production 

wastewaters currently being treated at our facility and 2) solicit proposal for the 

..;_ .. :·installation of a 200,000 gallon equalization tank. 

The purpose of the NPDES permit effort is to remove these oil and gas 

production wastewater streams from the discharge to the POTW and increase our flow 

capacity for septage handling. 

Since the City of Wheeling is now obligated to limit our discharge flow to 

200,000GPD with an interim limit of235,000GPD until January 2009, LAD must fmd 

other means to maintain its position in the marketplace. Currently, LAD is in contact with 

the WVDEP in Charleston, requesting guidance in preparing our NPDES application. As 

with all such permits, LAD estimates that a minimum of 6-12 months is required just to 

obtain a "draft" permit response ftom the Department. 

Esso-svl.-vc:n c1s~:1o ao s~ ..J~W 
Page2 of2 

However~ LAD will press WVDEP to indicate whether such a discharge into 

Wheeling Creek is feasible early in the permit process. As LAD indicated during our 

meeting the decision of the WVDEP wiU MANDATE our course of action. Their 

-. discharge limitations will determine the economic feasibility of treatment in meeting the 

NPDES discharge requirements. Meanwhile, LAD needs time to explore this and other 

options to comply with the new Permit modifications just recently issued by the City Of 

Wheeling. 

As indicated during our meeting, an additional treatment process, anticipated, as 

either sand filtration or Dissolve air flotation will be required. Although not a formidable 

task, LAD will still need time to order and install additional equipment. 

In sununary, LAD is fully committed to improving the quality of wastewater 

being discharged to the City Of Wheeling and we have proven that by ordering new 

dewatering equipment sized to treat all the septage flow entering our facility. A copy of 

our equipment order was presented during the meeting of 3/18/08. Also, LAD has begun 

to prepare a NPDES permit application following the instructional guidelines of the 

WVDEP. Time is required to complete this application and obtain a response from the 

Department. The response of the WVDEP to our NPDES application will determine our 

ultimate course of action 

However, within the nine (9) month interim flow limitation allowed, LAD will 

install a new technology for solids dewatering, research the possibility of a NPDES 

discharge pennit and explore the equalization options for storing wastewater. LAD will 

provide progress reports to the City on our interim compliance schedule throughout the 

nine-month flow reprieve as a good faith effort of activity and resulting decisions. 

After review of the minutes of the our meeting of 3/18/08 as recorded by your 

Fran Adams, LAD is in agreement with the information and included as an 

ATTACHMENT hereto. 

Attachment, WPCD minutes 

ESSO-Svl.-v~l. 
'· ·; L' 'd A t I '' •• 11 I. ) ) ) j ~ ' o I \ ' ' ' ' ' ' L :· · lqUI SSe S :1 .,t;. ·,,~·), · .. ·.·::·,.,,., ;/,··,(r /n 

- . 

June 10, 2008 

226 Rankin Road, Washington, PA 15301 

phone: 304-233-1783 fax: 304-233-1785 

Mr. A. King Campbell 

Plant Superintendent 

City Of Wheeling- WPCD j ' .,M L l 2l!ud ------ 26rlh~rurrstt~ ---------------------·--~-=~---~----------------

p .0. Box 6348 

Wheeling, WV. 26003 

Subject: LAD Pre-treatment Plant Improvements 

Progress Report 

Dear Mr. King: 

This progress report is in accordance to our agreement of understanding during 

our meeting of 3/18/08 to provide periodic updates on the construction schedule of our 

improvements to the plant. To date LAD has accomplished the following milestones: 

1. Ordered Rotary Press manufactured by FOURNIER on 3/25/08. Since placing 

the order, drawing approval and modifications have been finalized and 

delivery of the unit has actually been accelerated. The press is expected for 

delivery the first week of JULY. In anticipation of this early press delivery, 

LAD has hired contractors to commence removal of the press that requires 

cranes, structural steel removal and opening the roof. The existing press 

expects to be taken out of service on June 25, 2008. 

2. Installation of the mew Rotary Press will begin immediately upon delivery. It 

is estimated that approximately 30-45 days will be required to install the press 

and all the support equipment (i.e. Electrical, polymer tank, sludge pumps, 

platform steel and painting). 

3. Start-up of the press is estimated to be during the seGond week in July. 

4. A 200,000-gallon Equalization and pH treatment tank was ordered 4/24/08. 

Drawing approval indicating "Release for Fabrication" was completed on 

6/3/08 and the tank is expected for delivery the first week in September. 

Gil"-' (ANtL Installation is schedule to be completed by 10/15/08. 

e-.¢ 5. Start-up and hydrostatic testing of the tank is anticipated by 10/31108 

6. A petition for an NPDES discharge was submitted to th.e WVDEP on 3/27/08. 

After several inquires and conversations with the Department, a BWQ plan 

was finally received on 5/30/08. LAD has been charged with sampling and 

flow monitoring Wheeling Creek for possibly 12 times or six (6) months 

before "draft" discharge limits will be issued. The sampling and flow 

monitoring oin is at the confluence of Wheeling Creek with the Ohio River 

located along MAIN Street between 16th & 17th Streets. LAD must submit a 

flow monitoring and sampling plan for approval to the State before LAD is 

Y~lDR -rQ ~N'\PCl tJ6--
Page2of2 

allowed to begin sampling. As of this writing, a sampling and flow plan is 

being prepared for submittal to the WVDEP. 

Mr. King, LAD is making good progress is maintaining our commitment to upgrade and improve our facility. After review of this information if you have any questions 

concerning our progress feel free to contact me at 724-350-2760. We antici ate 

submitting our next progress report sometime in August after the Rotary ress is 

installed. 

Cc; Chuck Neuhardt, WPCD 
CITY OF WHEELING 

~ ~ 

2516 MAIN STREET 

P.O. BOX 6348 

WHEELING, WEST VIRGINIA 26003 

•

Tf 

0 ~ 

------------4~ ~ 1:) 

~-------------------------------------------------------------

~ 

,['f Vl\1.()~ 

March 7, 2006 

Dear Septage Hauler: 

Water Pollution Control Division 

(304) 234-3874 (Telephone) 

(304) 234-3873 (FAX) 

fit4ak@aol.com (e-mail) 

We are sorry to inform you that Wheeling's Water Pollution Control Division (WPCD) will 

not be able to accept any outside waste or septage effective April 1, 2006 until further 

notice due to the current construction project at the plant and the installation of new bar 

screens. We will notify you by letter when we will be able to accept septage dumping. 

We apologize for the inconvenience. If you need any more information or have any 

questions, please contact me (304) 234-387 4. 

~~ WPCD Superintendent 

cc: Russell Jebbia, Public Works Director 

Michaeline Raskiewicz, Accounting Supervisor 
----

: • 'I fl. ... ~ . ,.t .......... .: ~ ..... .. • ...... 

"' ... r • • :.:--. , ·...: I ::.-fi Z I • "' 

p .:-( ... ~:' :. • -t-.. ,. -"-.L 

• 

I 

• 

I 

II 

~ .r 1.-r-JI.r~- ·.r--c 

.. .. . :- . ·: ...... . . .... ..--:-~~ .. 

. .. .. . . : "· .. ,. .,. • • • • F 

• ...,.: .... .. 'H.IIIIIIIQI i 

• tr.- .... 

• • • 

• 

I 

• 

•• 

... ... .. -

.. 

•• 

• 

• 

II II 

II 

-

I 

, 

• 

• 

• 

• I 

• • 

• 

• • 
SURCHARGE INVOICE COMPUTATION 

QUARTER: 4th- 00 

PERMIT: #0014 

LIQUID ASSETS DISPOSAL INC. 

99 PENINSULA STREET 

WHEELING WV 26003 

CHARGES FOR B.O.D. CONCENTRATION: 

ENTER FLOW: 

ENTER B.O:D. 

TOTAL 8.0.0. 

FEE: 

JOU_OO (FIRST 300) 

243.8l (GREATER THAN 300) 

543.83 

$857.58 

CHARGES FOR T. S. S. CONCENTRATION: 

ENTER FLOW: 7,809,566.00 

ENTER T.S.S. 356.00 (FIRST 350) 

118 .. 66 (GREATER THAN 350) 

TOTAL T.S.S. 468.66 

FEE: $2,743.63 

GRAND TOTAL: 
II 

SURCHARGE INVOICE COMPUTATION 

"ID'SNAMB 

ADDRESS · 

t 0 o. \tf 

PERMIT NUMBER 

Measured Flow x 8 . 34 

1,~,000 

DATE , 

D~e. a <4' · 

Nov' o<o' 

fAVO. 

DATE 

QUARTER 

O\ I o4./o-z · ·- · - - · DATE 

BEGINNING FLOW = 

gal 

ga1 

g_al 

aal 

gaJ 

TOTAL 

TOTALWBIOHI 

lb/mgfl 

MEASURED FLOW 

3o cPq ~ qd() gal :t 3']_~ • ~,,~ B!! ~. (/&tJ. tp-() sat 

~ 

sat 

Z, 8rJ9.. ~~~ 

CHARGES FOR B.O.D. CONCBNTRATION 

TOTALB.O.D. : ___ mgll""'" 

- . 

FIRST (300) : __ ...;..;.mg/1&,; 300FRBB 

' RHMAINDER: __ ...;;;;;mrll;g;,; $0.05.4/lb. 

, TOTALB.O.D.FBE: 1!::::11 $!=· ========.!·II !===~=Otal=W=e=igb=t====x==B=.=o.=D=. =x=Ra=te===Fi=ec===.JH ... 

SCHEDULE 

DATE RESULT CHARGES FOR T.S.S. CONCBNTRATION - TOTALT.S.S. : mgfl 

FIRST (350) : mg/1 ------ 3SOFRBB 

RHMAINDER : ___ m..¥.ogll $0. 35 5/1 b. 

Total Weiiht x T.S.S. · x Rate = Fee 

TOTAL T.S.S. FBB : l!:::ll $======!111 

_ _.....,_ TfYrAL RO.D. FRR +TOTAl~ T.S.S. FRR =·'T'CYrAT. r.RAlUlR ~ · t , 
II 

l 

SURCHARGE INVOICE COMPUTATION 

t:!lU'SNAME 

ADDRESS 

ff 00/L/ 

PERMIT NUMBER 

Measured Flow x 8 . 34 

l,<¥JO,OOO 

. ' 

= Total Wci~t 

DATE ENDING FLOW - DATE 

SCHBDULB SELF · 

DATE RESULT ·I DATE RESULT 

mg/J 1_?}_-_j"'_f~ -~e-~ mgll 

mgll ' m~ 

:mg/1 . mg/1 

mvJJ mgll 

QUARTER 

01 /rY'-1 /e1 

DATE 

HB !31ZB If TOTAL WBIGHI 

lb/mg/1 

BEOINNING FLOW = MEASURED FLOW 

gal gal 

&!!! 

----- sat 

8!! 

gal gal 

TOTAL 7~ 8aq t :s-~fA 

CHARGES FOR B.O.D. CON CENTRA nON 

-iurALB.O.D. : ~y~,~Jmg11 

FmST(300) : )6{) mg/1 300FREB 

~BR: ~q3,S3mrft $b.o5.4/lb. 

fAVG. 5'13 I 8"3 I I TOTALB.O.D.FBB : I~ f!J;JJ. 5-'Z .I 

!:===~=Otal==W=ei=gb=t==:x.=B=.o=.D=·=· x=R==ate=====Fi=ec===.t" . . ,. SCHEDULE SELF 

DATE RBSULT CHARGES FOR T.S.S. CONCENTRATION I DATE RESULT 

mgll rdiJtJ to(g - ti~9J mgll 

mgl.l . mg/1 rorAL:T.s.s. : L{ ~S, fie mfft 

mgl.l mg/1 

~ mg/J mg/1 FIRST (350) :. )':5o mgll 350 FRBB 

REMAINDER: //8,~~80 $0.355/lb . 

... [ Tolal Weight x T.S.S. · x Rate = Fee 

II . ............... TOTAL B.O.D. FRR + TafAT .. T.S.S. FJm =.TOTAl. ffiAROR ~ . l ' 3 (aO I. d I 
SURCHARGE INVOICE COMPUTATION 

QUARTER: Jrd-.05 

PERMIT: #0014 

LIQUID ASSETS DISPOSAL INC. 

99 PENINSULA STREET 

WHEELING WV 26003 

CHARGES FOR B.O.D. CONCENTRATION: 

ENTER FLOW: 10 .. 224 .OOOUQ)[· 

ENTER B.O.D. 300.00 (FIRST 300) 

966 2:l (GREATER THAN 300) 

TOTAL B.O.D. 1,266.25 

FEE: $11,534.65 

CHARGES FOR T. S. S. CONCENTRATION: 

ENTER FLOW: 10,224,000.00 

ENTER T.S.S. 35()_00 (FIRST 350) 

1.,088 .. 00 (GREATER THAN 350) 

TOTAL T.S.S. 1,438.00 

FEE: $14,565.17 

GRAND TOTAL: $26,099.82 
SURCHARGE INVOICE COMPUTATION 

L IQ u 1 D AS\{( .. Dl0\)o,s ~L 

SID'S NANJE 

~q ?e-N\ ~'duL-~ t:Q\~ t- ADDRESS 

~))V-t · 

PERMIT NUMBER 

Measured Flow x 8 . 34 

1,000,000 

SCHEDULE 

DATE RESULT 

QUARTER 

\O I 

DATE1 

= Total Weig~t 

/ Q(o I 

TOTAL WEIGHT 

lb/mg/1 

DATE BEGINNING FLOW = MEASURED FLOW 

gal 3 ,& f3 /, Cj<XJ gal 

--------~~------~ 

------lf--------"ga"-1 3. & 71, Zoo gaJ 

--------~-------~g~al ~o.ioo gru 

gal gal --------~~~----~ 

gal gal --------~~------~ 

mgll 

TOTAL 

CHARGES FOR B.O.D. CONCENTRATION 

TOTAL B.O.D. : t'J..&~ ·~ ~ mg/l 

FIRST (300) : 3oo mgll 

REMAINDER : 14~,¢ 'Jmg/1 

300FREE 

$.140/lb 

!Avo._ l:;2 u{e/~'§."~ l TOTALB.O.D.FEE: 11$ l\( 3t~, k5 

Total Weight x B.O.D. x Rate = Fee II . ,. .II 

. mgll 

mg/1 

mgll 

Total Weight x T.S.S. x Rate == Fee 

CHARGES FOR T.S.S. CONCENTRATION 

TOTALT.S.S. : 14 5S mg/1 

FIRST (350) : :S S D mgll 

REMAINDER : \ 0 ~ ~ mg/1 

·~ 

350FREE 

$.157/lb 

TOTAL T.S.S. FEE :II$ I q, §Zt~ . \l 

~'-TOTAL B.O.D. FRR +TOTAL T.S.S. FRR = TO'T'AL C:HARrm ~ ~ d/.e, QCjY, 8?.. 
SU.RCHARGE INVOICE COMPUTATION 

QUARTER: 2ND- 06 

PERMIT: #0014 

LIQUID ASSETS DISPOSAL INC. 

99 PENINSULA STREET 

WHEELING WV 26003 

CHARGES FOR 8.0.D. CONCENTRATION: 

ENTER FLOW: 8.432.500.00 

ENTER 8.0.D. 300.00 (FIRST 300) 

800J)0 (GREATER THAN 300) 

TOTAL 8.0.D. 1 '100.00 

FEE: $7,876.63 

CHARGES FOR T. S. S. CONCENTRATION: 

ENTER FLOW: 8,432,500.00 

ENTER T.S.S. 350.00 (FIRST 350) 

799_00 (GREATER THAN 350) 

TOTAL T.S.S. 1,149.00 

FEE: $8,822.04 

GRAND TOTAL: $16,698.67 
ADDRESS 

.$:0 0 \ i:. 

SURCHARGE INVOICE COMPUTATION 

QUARTER 

07 - I'd - 0~ 

DATE 

PERMIT NillvfBER 

II 

II 

Measured Flow x 8 . 34 

1,000,000 = Total Weig~t 

DATE ENDING FLOW DATE 

Sv~ ~ J..,\ oa gal 

\Y\~j 31 '3], Sao gal 

. \1?C2-\ L- _2~ {aoo gat 

!!:al 

gal 

SCHEDULE SELF 

DATE RESULT I DATE RESULT - olf/1~/ olD 8\0 mg/J O(o /d.C9/ C){e f337 mg/1 

mg/J 05 .31 /O~ \L{ 13 mgll 

mgll CJL-! /~0 i 6(a ~aso. mgll 

mdl mg/1 

AVO. ! 100 IMTV 

I 

Total Weight x B.O.D. x Rate = Fee 

SCHEDULE SELF 

DATE RESULT I DATE RESULT 

Ol// l8/ a(o . I l-L1R mgtt or ~Fil~Tot.o · \050 mg/I 

mg/1 ·o'5./'3t/ O(c 18~ · mg/l 

•' mg/1 04 l ().(o f Ol.o I 'S l d.- mgll 

mg/1 mgll 

. 

Total Weight x T.S.S. · x Rate = Fee 

I 

TOTAL WEIGHT 

lb/mg/1 

BEGINNING FLOW = MEASURED FLOW 

gal :11 ~I d- 1 100 gal 

ga1 J, L3Z~ 8oo gal 

gal !J.~B ~, &oo ~a! 

e:al gal 

gftl gal 

TOTAL 8 l L(3;l.. 1 '5_ oO 

CHARGES FOR B.O.D. CONCENTRATION 

TOTAL B.O.D. : //00 mg/1 

FIRST (300) : 3o D mg/1 300 FREE 

REMAINDER: '3 0Q . mg/1 $.140/lb 

TOTAL B.O.D. FEE :II$ 1. 811JJ. 3 II • \ ' 

CHARGES FOR T.S.S. CONCENTRATION -~ 

TOTAL T.S.S. : II 4 q mg/1 

FIRST (3SO) : ~~0 mg/1 

REMAINDER: L q 9 mg/1 

350FREB 

$.157/lb 

TOTAL T.S.S. FEE : 11$ <(?),3~~. olt' · 

_ _.. .____TOTAL B.O.D. FER+ TOTAL T.S.S. FP.H = ·TOTAL rHARC1F. ~ ~ ~~~ ~q~, {a\ 
SURCHARGE INVOICE COMPUTATION 

QUARTER: 1st- 06 

PERMIT: #0014 

LIQUID ASSETS DISPOSAL INC. 

99 PENINSULA STREET 

WHEELING WV 26003 

CHARGES FOR B.O.D. CONCENTRATION: 

ENTER FLOW: 7.847.100.00 

ENTER 8.0.0. 300JJO (FIRST 300) 

577.50 (GREATER THAN 300) 

TOTAL B.O.D. 877.50 

FEE: $5,291.21 

CHARGES FOR T. S. S. CONCENTRATION: 

ENTER FLOW: 7,847,100.00 

ENTER T.S.S. 350.00 (FIRST 350) 

955.00 (GREATER THAN 350) 

TOTAL T.S.S. 1,305.00 

FEE: $9,812.47 

GRAND TOTAL: $15,103.68 
II 

SURCHARGE INVOICE COMPUTATION 

SIU'SNAME 

~9 ttNll-t~vt..A fJ\1.\\{f 

ADDRESS 

~ oa \~ . PERMIT NUMBER 

Measured Flow x 8 . 34 

1,0,00 000 = Total Weig~t 

DATE , ENDING FLOW DATE 

1'1\AiL _l,! iCl '5"' G- 0 gal 

.rf-'B. :E> 1:( :.) c1 , ,; gal 

~o"-1 1- S3.'-{ '1oo gal 

gal 

gal 

SCHEDULE SELF 

DATE RESULT I DATE RESULT 

1./1 /o&, 15q() mg/1 .5 !30 /at, /&5' mg/1 

mg/1 mg~l 

mg/1 mg/1 

. mg/1 mg/1 

BEGlNNING FLOW 

gal 

gal 

gal 

gal 

gal 

TOTAL 

QUARTER 

o=t I ~s I ote 

DATE t 1 

TOTAL WEIGHT 

lb/mg/1 

= MEASURED FLOW 

5 o-z9 "5a-o gal 

~ "-(5-:J.. qe:o gal 

~~s~ ]aa gal 

gal 

&al 

7 B':L 2 LO () 

CHARGES FOR B.O.D. CONCENTRATION 

TOTALB.O.D. : 871,5 mg/1 

FIRST (300) : 3oo mg/1 

REMAINDER : ~ ll ,'5 mg/1 

300FREE 

$.140/lb 

fAvo._ S 1\ ,t5 n"\\ K I I TOTALB.O.D.FEE :I$ ;i~9 I ,d..\ 

Total Weight x B.O.D. x Rate = Fee II \ 

SCHEDULE SELF 

DATE RESULT I DATE RESULT 

7-/ 7 /{)~ . , .,_ 3 0 mg/J '3 /3o /o& 3 80 mg/1 

mgll . . mg/1 

.. mg/1 mg/1 

mg/1 mgfl 

I AVO. \:se-a._ ""\Q 

Total Weight x T.S.S. x Rate = Fee H 

CHARGES FOR T.S.S. CONCENTRATION 

TOTALT.S.S. : \3a~ mg/1 

FIRST (350) : ~ "5 C) mg/1 

REMAINDER : '1 '5 ~ mg/1 

~ 

3SOFREB 

$.157/lb 

TOTALT.S.S.FEE: I!$ Cf81:l..~Y'7 II 

/'~. TOTAL RO.D. FER+ TOTAL T.S.S. FRH = ·TO'l'AT. rHARfffi ~ ~ l~ 105.~8 J 
SURCHARGE INVOICE COMPUTATION 

QUARTER: 1st -07 

PERMIT: #0014 

LIQUID ASSETS DISPOSAL INC. 

99 PENINSULA STREET 

WHEELING WV 26003 

CHARGES FOR 8.0.0. CONCENTRATION: 

ENTER FLOW: 11 ,559,600.00 

ENTER 8.0.D. 300.00 (FIRST 300) 

215.40 (GREATER THAN 300) 

TOTAL 8.0.0. 515.40 

FEE: $1 '121.37 

CHARGES FOR T. S. S. CONCENTRATION: 

ENTER FLOW: 11 ,559,600.00 

ENTER T.S.S. 350.00 (FIRST 350) 

527.00 (GREATER THAN 350) 

TOTAL T.S.S. 877.00 

FEE: $18,036.32 

GRAND TOTAL: $19,157.69 
SURCHARGE INVOICE COl'A:PlUTATION 

J'SNANJE 

ADDRESS 

PERMIT NillvfBER 

Measured Flow x 8 . 34 

1,000,000 

DATE 

SCHJIDULE 

DATE RESULT ' 

OJ.' "J.1. 07 

1!-J.C, 

= Total Wei~t 

DATE 

al 

\:s\·o r 

QUARTER 

ot 

DATE 

BEGINNING FLOW = 

gal 

gal 

gal 

gal 

TOTAL 

TOTALWEIGm 

lb/mg/1 

MEASURED FLOW 

5< '1.!3 9 ( 0 gaJ 

3 d.. 'I 3 7oc) gal 

d4> ~:Qoo gal 

gal 

gal 

CHARGES FOR B.O.D. CONCENTRATION 

TOTAL B.O.D. : 5 IS /{ D mgll 

FmST (300) : 100 rog/J 300 FREE 

~ER: ;15 ;((} n1g() $0.05.4/lb. 

I A v~. Sf S/·10 ti; a I I T TOTAL B.O.D~ FEE : I $ II (fi f I 3 '1 

===· ='t=o=tal=W=a=· g=h=t =x= B=.O=·=D=. =x=Ra==te=-=-=B=ee====.:!.JIJ . - . 

.II 

SCHEDULE 

DATE RESULT - SELF 

DATE RESULT CHARGES FOR T.S.S. CONCENTRATION 

TOTAL'T.S.S. : 

i) 7"'1 

u ( mgll 

mgll 

Jng/l FJRST (350) : 3 .. 50 mg/l 3SOFRHB 

REMAlNDER: SJ:7 mg/1 $0 . 355/lb. 

Total Weigbt x T.S.S. · x Rate = Fee lj 

TOTAL T.S.S.FEE :II$ { §o:3 U .J.,_. 

,, 

. ----- --- 'TOTAl~ B.O.D. FHR +TOTAl~ T.S.S. FHR = ' 'l'O'l'Al. r.HARnR ~ !t 

'I q! I "J11' {;! (.i 
SURCHARGE INVOICE COMPUTATION 

QUARTER: ~~~-07 

PERMIT: #0014 

LIQUID ASSETS DISPOSAL INC. 

99 PENINSULA STREET 

WHEELING WV 26003 

CHARGES FOR 8.0.D. CONCENTRATION: 

ENTER FLOW: 13,582,800.00 

ENTER 8.0.D. 300.00 (FIRST 300) 

11.70 (GREATER THAN 300) 

TOTAL 8.0.D. 311.70 

FEE: $71.57 

CHARGES FORT. S. S. CONCENTRATION: 

ENTER FLOW: 13,582,800.00 

ENTER T.S.S. 350.00 (FIRST 350) 

504.70 (GREATER THAN 350) 

TOTAL T.S.S. 854.70 

FEE: $20,296.31 

GRAND TOTAL: $20,367.88 
SURCHARGE INVOICE COMPUTATION 

J'SNAMB 

cv~ C:~\~ SVLft .$T<?lfT 

ADDRESS 

-~~=oo;Lf PERMIT NUMBER 

:· Measured Flow x 8 • 34 1,~,000 = Total Wei~t 11 

-·I 

J_UD QT(L 

QUARTER 

D\ I \' /oJ 

DATE 

TOfALWBIGm 

lb/mg/1 

DATE ENDING FLOW DATE BEGINNING = MEASURED FLOW 

gal 

gal 

--- gal 

gal 

TOT-¥-

CHAR ES FORB.OD. CONCBNTRATION 

SCHEDULE SELF 

DATE RESULT ·I DATE RESULT TOTALBOD.: 

FmST 300): .., mg!J ~I!Bio7 ~~ -mgn .. . 

mgll m~ 

mg/1 . mg/1 

oWl mg/1 

I 

REMAINDER: 

300FREB 

\\,1.mgll $0.05.4/lb. 

. 

I Avo. ,51 \, J '!"41 J TOTALB.o.D.FHE :(Is ,,,s-,. .11 

===~=Otal=W==ei=gh=t=x=B=.O=.D=·=x=R=at=e=====Fi=ee====.JIJ . . ,. . 

SCHEDULE · SELF 

DATE RESULT I DATE RESULT . CHARr FOR T.S.S. CON~~ON 

. ·- ' mgll 0k/JB/o7 '.8«1-Co mgll .,.· - rng/.1 . mg/1 

mg/1 mgll 

rngll rng/I 

TOTALT.S.S. : g5lj ,7 mg11 : 

FIRST l35o) :· 3SD mgll 350 FRHB 

IAVG. .... ..,. ••.• ,...,., .. _.HR: ioY L 1 mgll $0 .355/lb. 

Total Weight x T.S.S. · x Rate = Fee lj 

TOTAL T.S.S ,FBB :II$ ,0, 0\Cj(R; 3/-

. ..-...... TOT AI .. n_o.n. FRR + TOT AT.. T.s.s. FHR = ·TOT AT. rHAkcm. ~ ~ 0 ~fe 1. BB 

I 
SURCHARGE INVOICE COMPUTATION 

/-1 0 u l a ~55~ T2) D\d-" 6 ~ ~L , 1_ N_e..,_. 

J'SNAME 

ADDRESS · 

* DD1Y 

PERMIT NUMBER 

Measured Flow x 8 . 34 

1,~,000 = Total Wei~t II 

QUARTER 

0"1 /II /o\ 

DATE r 1 

TOTAL WBIGHI 

lb/mg/1 

DATE 

0uN~ 

DATE BEGJNNING FTIOW = MEASURED FLOW 

j gal s ,3f1 1 46:6 gal 

J;i41B ~~-g : 

) . 

l ga] 

I gal 

Ral gal 

gal gal 

131 SB;A. 8l)o I 

TOT¥--

CHARGES FOR B.O.D. CONCENTRATION 

SELF . I 

TOTAL B.OD. : __ __;;;;;mg/1£; 

FmsTI(3ciol : __ _;.;;togll;g,; 300 FREE 

REMAJjNDHR : __ __;;;:m:g:,;gll $0.05.4/1 b. 

IAVO. 

TarAL·t.S.S. : mg/1 

I 

FIRSTt(350) : ___ m.::...g/1 3SOFREB 

IA.VO. ~ER : __ ___;_m;g_tg/J. $0. 35 5/1 b. 

- ~~~~========~========~ .. Total Weight x T.S.S. -x Rate = Fee lj 

TOTAL T.S.S~ FEB : t=ll $======::!Ill 

. .---..... _TOTAl. R.O.D_ FER+ TOTAl. T.S.S. FRR =-TOTAl. r.RARGR . i ' 
SURCHARGE INVOICE COMPUTATION 

QUARTER: 1st -07 

PERMIT: #0014 

LIQUID ASSETS DISPOSAL INC. 

99 PENINSULA STREET 

WHEELING WV 26003 

CHARGES FOR B.O.D. CONCENTRATION: 

ENTER FLOW: 18,573,100.00 

ENTER B.O.D. 300.00 (FIRST 300) 

1,230.16 (GREATER THAN 300) 

TOTAL B.O.D. 1,530.16 

FEE: $10,289.77 

CHARGES FOR T. S. S. CONCENTRATION: 

ENTER FLOW: 18,573,100.00 

ENTER T.S.S. 350.00 (FIRST 350) 

2,988.77 (GREATER THAN 350) 

TOTAL T.S.S. 3,338.77 

FEE: $164,350.60 

GRAND TOTAL: $174,640.37 
II 

SURCHARGE INVOICE COMPUTATION 

SIU'SNAME QUARTER 

ADDRESS 

It> /?:,I Ol 

DATE1 I 

* 001~ PERMIT NUMB'ER .. 

Measured Flow x 8 . 34 

l,C¥JQ,OOO = Total Weig~t II u TOTAL WEIGH'! 

lb/mg/1 

DATE ENDING FLOW 

gal 

gal 

gal 

gal 

SCHEDULE 

DATE RESULT ·I DATE 

Ol./3o/Ol IR'lD mg/J 

ol/':J.o/ 07. 33S mg/1 

mg/1 

mg/1 

IAVO . . 

DATE BEGINNING FLOW = :MEASURED FLOW 

gal gal 

gal gal 

gal gal 

gal 

gal gal 

TafAL 

CHARGES FOR B.O.D. CONCENTRATION 

SELF 

RESULT TOTAL B.O.D. : ___ mg/1...._ 

mg/1 

mg{l FIRST (300) : ___ m..-g/J 300 FREE 

. mgll 

mgll 

RHMAJNDER: ---=m.,..g/1 $0.05.4/lb . 

TOTAL B.O.D. FEE : 1'-=1 $=======::::!.1·'1 

IU:I =====To:::::tal===W=et~· g~bt===::x:.::::=::B=.O=.D=·=x===Ra==te=====Fi=ee===:!J~~ . ,. 

SCHEDULE SELF CHARGES FOR T.S.S. CONCENTRATION DATE RESULT I DATE RESULT - . 

ol/30/07 . 4/~ '/0 mg/1 mgll 

01/"0 I 01 to'i(;. mgll . mg/1 TOTAL' T .S.S. : mg/1 • ' mg/1 mgll 

mgll mgll FIRST (350) : 

----mg/1 3SOFRHB 

IA.VG. REMAJNDER : ___ m...._gll $0. 35 5/1 b . 

li:--:;=======T=o=tal=W===ei~gh=t=x==T=.S=.S=. =· x~R=at=e====F=ee====::!Jij TOTAL T.S.S. FEB :f t.=l $======:::!1'' . _...-,_TOTAL R.O.D. FF.E +TOTAL 1'.S.S. FRR =·TOT'Al. rHAlUiR ~ · ~ ,