CO Emissions Analysis: O2 vs. Damper Position

OFA Portion to Total Airflow (%) 1COAXI172B

Hour of Operation: 720 Inlet Damper Positions (%open)

Tons of CO 45.99 SW Damper 1SGBKS156B

Average Hourly Rate127.74 SE Damper 1SGBKS158B

Data Repl. Ratio (%) NW Damper 1SGBKS160B

System Shut Down 0.00 NE Damper 1SGBKS162B

Substituted Data 0

East Side O2 1COAXI079A

Start Time Interval

9/1/06 0:00 0:15:00

Run Date Period East Side West Side

Boiler Excess 

O2%

9/26/06 0:00 2.57 2.81 2.69

9/26/06 0:15 2.66 2.81 2.72

9/26/06 0:30 2.63 2.90 2.78

9/26/06 0:45 2.58 2.91 2.74

9/26/06 1:00 2.48 2.90 2.68

9/26/06 1:15 2.48 3.12 2.79

9/26/06 1:30 2.56 3.16 2.85

9/26/06 1:45 2.66 3.20 2.95

9/26/06 2:00 2.53 3.27 2.91

9/26/06 2:15 2.56 3.26 2.92

9/26/06 2:30 2.61 3.28 2.95

9/26/06 2:45 2.94 3.47 3.22

9/26/06 3:00 3.20 3.66 3.43

9/26/06 3:15 3.61 3.88 3.74

9/26/06 3:30 3.39 3.84 3.62

9/26/06 3:45 3.03 3.56 3.30

9/26/06 4:00 2.80 3.30 3.03

9/26/06 4:15 2.61 3.18 2.88

9/26/06 4:30 2.69 3.23 2.96

9/26/06 4:45 2.73 3.16 2.95

9/26/06 5:00 2.72 3.11 2.90

9/26/06 5:15 2.67 3.16 2.94

9/26/06 5:30 2.71 3.19 2.93

9/26/06 5:45 2.66 3.26 2.95

9/26/06 6:00 2.62 3.23 2.92

9/26/06 6:15 2.56 3.22 2.92

9/26/06 6:30 2.70 3.20 2.94

9/26/06 6:45 2.67 3.14 2.92

9/26/06 7:00 2.61 3.21 2.90

9/26/06 7:15 2.64 3.20 2.91

9/26/06 7:30 2.70 3.07 2.86

9/26/06 7:45 2.65 3.00 2.81

9/26/06 8:00 2.65 2.94 2.80

9/26/06 8:15 2.68 3.02 2.84

9/26/06 8:30 2.69 3.06 2.88

COMPLIANCE CALCULATION

Unit 1 PI Tags

O2 Values
9/26/06 8:45 2.68 3.00 2.84

9/26/06 9:00 2.63 3.01 2.81

9/26/06 9:15 2.59 2.99 2.80

9/26/06 9:30 2.65 2.90 2.78

9/26/06 9:45 2.61 2.95 2.79

9/26/06 10:00 2.54 2.94 2.75

9/26/06 10:15 2.61 2.90 2.75

9/26/06 10:30 2.51 2.95 2.73

9/26/06 10:45 2.63 3.01 2.83

9/26/06 11:00 2.51 2.67 2.59

9/26/06 11:15 2.56 2.94 2.74

9/26/06 11:30 2.65 2.30 2.47

9/26/06 11:45 2.66 2.40 2.56

9/26/06 12:00 2.74 2.88 2.82

9/26/06 12:15 2.77 3.05 2.90

9/26/06 12:30 2.74 3.26 3.01

9/26/06 12:45 2.72 3.19 2.94

9/26/06 13:00 2.71 3.15 2.96

9/26/06 13:15 2.75 3.24 3.00

9/26/06 13:30 2.68 3.33 3.01

9/26/06 13:45 2.56 3.17 2.92

9/26/06 14:00 2.63 3.17 2.91

9/26/06 14:15 2.58 3.12 2.86

9/26/06 14:30 2.59 3.08 2.82

9/26/06 14:45 2.59 3.04 2.80

9/26/06 15:00 2.58 3.09 2.85

9/26/06 15:15 2.59 3.04 2.82

9/26/06 15:30 2.67 3.02 2.84

9/26/06 15:45 2.53 3.06 2.80

9/26/06 16:00 2.48 3.13 2.81

9/26/06 16:15 2.40 3.16 2.78

9/26/06 16:30 2.84 3.35 3.09

9/26/06 16:45 2.33 2.92 2.63

9/26/06 17:00 2.19 3.10 2.65

9/26/06 17:15 2.34 2.89 2.62

9/26/06 17:30 2.93 3.24 3.09

9/26/06 17:45 3.03 3.52 3.26

9/26/06 18:00 2.91 3.37 3.15

9/26/06 18:15 2.79 3.12 2.97

9/26/06 18:30 2.76 2.75 2.74

9/26/06 18:45 3.03 2.58 2.81

9/26/06 19:00 2.94 2.56 2.75

9/26/06 19:15 2.78 2.65 2.73

9/26/06 19:30 2.92 2.51 2.70

9/26/06 19:45 2.80 2.76 2.76

9/26/06 20:00 2.80 3.04 2.92

9/26/06 20:15 2.74 3.05 2.92

9/26/06 20:30 2.75 3.05 2.91

9/26/06 20:45 2.78 3.09 2.89

9/26/06 21:00 2.76 3.05 2.89

9/26/06 21:15 2.74 2.98 2.87

9/26/06 21:30 2.71 2.99 2.85
9/26/06 21:45 2.70 2.94 2.81

9/26/06 22:00 2.72 2.98 2.86

9/26/06 22:15 2.72 2.96 2.83

9/26/06 22:30 2.73 3.00 2.89

9/26/06 22:45 2.84 3.04 2.95

9/26/06 23:00 2.94 3.11 3.03

9/26/06 23:15 2.97 3.12 3.02

9/26/06 23:30 2.97 3.10 3.05

9/26/06 23:45 2.87 3.19 3.02
OFA Total Flow (kpph) 1COAXI172C

1/3 Port Damper Positions (%open)

SW Damper 1SGBKS164B

SE Damper 1SGBKS166B

NW Damper 1SGBKS168B

NE Damper 1SGBKS170B

West Side O2 1COAXI080A

OFA Portioned 

Flow (% of total) Total OFA Flow Plenum Inlet 1/3 Port

3.0 220.14 98.4 2.5

2.9 221.30 98.4 2.5

3.0 217.55 98.4 2.5

2.9 213.21 98.4 2.5

2.9 220.26 98.4 2.5

2.8 214.45 98.4 2.5

2.9 214.95 98.4 2.5

2.9 214.06 98.4 2.5

2.9 226.95 98.4 2.5

3.0 222.26 98.4 2.5

2.7 214.76 98.5 2.5

2.8 210.89 98.5 2.5

3.0 211.97 98.5 2.5

2.9 199.50 98.5 2.5

2.7 184.67 98.5 2.5

2.6 192.94 98.5 2.5

2.9 210.16 98.5 2.5

3.0 228.91 98.5 2.5

3.0 227.91 98.5 2.5

3.1 230.65 98.5 2.5

3.0 227.14 98.5 2.5

3.0 228.40 98.5 2.5

2.9 227.01 98.5 2.5

2.9 224.56 98.5 2.5

2.8 222.79 98.5 2.5

3.0 226.91 98.5 2.5

3.0 231.46 98.5 2.5

2.9 229.25 98.5 2.5

3.0 222.32 98.5 2.5

2.9 226.16 98.5 2.5

3.0 227.58 98.5 2.5

3.0 223.59 98.5 2.5

2.9 224.86 98.5 2.5

3.0 230.94 98.5 2.5

3.1 229.97 98.5 2.5

OFA Operating Status
3.1 232.86 98.5 2.5

3.1 231.93 98.5 2.5

2.9 227.33 98.5 2.5

3.1 227.47 98.5 2.5

3.1 229.54 98.5 2.5

3.1 232.85 98.5 2.5

2.9 225.89 98.5 2.5

3.1 232.45 98.5 2.5

3.2 235.29 98.5 2.5

3.1 234.03 98.5 2.5

3.0 237.46 98.4 2.5

3.0 237.54 98.4 2.5

2.8 239.85 98.4 2.5

3.3 240.80 98.4 2.5

3.2 236.50 98.4 2.5

3.1 239.13 98.4 2.5

3.1 236.98 98.4 2.5

3.1 240.72 98.4 2.5

3.2 238.03 98.4 2.5

3.2 241.73 98.4 2.5

3.0 231.86 98.4 2.5

3.1 232.50 98.4 2.5

3.1 240.54 98.4 2.5

3.1 232.27 98.4 2.5

3.0 227.37 98.4 2.5

3.0 225.85 98.4 2.5

3.0 226.88 98.4 2.5

3.1 233.87 98.4 2.5

3.1 223.84 98.4 2.5

3.0 226.49 98.3 2.5

3.2 229.64 98.3 2.5

3.2 241.12 98.3 2.5

3.4 242.52 98.3 2.5

3.2 240.48 98.3 2.5

3.1 242.44 98.3 2.5

3.1 226.36 98.3 2.5

3.1 227.73 98.3 2.5

3.1 233.51 98.3 2.5

2.9 209.34 98.3 2.5

2.7 196.95 98.3 2.5

3.0 205.68 98.3 2.5

2.7 203.04 98.3 2.5

4.0 295.70 98.3 2.5

6.6 480.00 98.3 2.5

9.0 657.00 98.3 2.5

9.9 721.80 98.3 2.5

10.0 714.23 98.3 2.5

10.0 718.25 98.3 2.5

10.0 724.36 98.3 2.5

10.0 722.63 98.3 2.5

10.1 723.94 98.3 2.5

10.1 720.85 98.3 2.5
10.1 720.30 98.3 2.5

10.2 720.49 98.3 2.5

10.2 724.30 98.3 2.5

10.2 722.35 98.3 2.5

10.3 719.00 98.3 2.5

10.3 730.69 98.4 2.5

10.3 743.90 98.4 2.5

10.3 748.86 98.4 2.5

10.4 743.88 98.4 2.5
2/3 Port Damper Positions (%open) Partitioned Flow (kpph)

SW Damper 1SGBKS165B SW Ports

SE Damper 1SGBKS167B SE Ports

NW Damper 1SGBKS169B NW Ports

NE Damper 1SGBKS171B NE Ports

Average Excess O2 1COAXI187A Heat Input

Boiler Data

2/3 Port Heat Input OFA Condition CO (ppm)

0.3 8574.3 No OFA 24

0.3 8542.1 No OFA 22

0.3 8545.3 No OFA 19

0.3 8542.0 No OFA 20

0.3 8563.5 No OFA 24

0.3 8501.4 No OFA 18

0.3 8523.6 No OFA 15

0.3 8544.2 No OFA 12

0.3 8542.9 No OFA 13

0.3 8544.3 No OFA 13

0.3 8517.6 No OFA 12

0.3 8219.8 No OFA 6

0.3 7948.4 No OFA 4

0.3 7750.7 No OFA 2

0.3 7534.2 No OFA 2

0.3 7851.3 No OFA 5

0.3 8225.1 No OFA 9

0.3 8575.9 No OFA 14

0.3 8606.5 No OFA 11

0.3 8612.6 No OFA 12

0.3 8599.9 No OFA 13

0.3 8607.0 No OFA 12

0.3 8604.7 No OFA 12

0.3 8601.3 No OFA 12

0.3 8598.5 No OFA 13

0.3 8608.6 No OFA 13

0.3 8606.6 No OFA 12

0.3 8607.8 No OFA 12

0.3 8596.3 No OFA 13

0.3 8615.0 No OFA 13

0.3 8602.3 No OFA 15

0.3 8615.0 No OFA 17

0.3 8607.0 No OFA 18

0.3 8610.2 No OFA 15

0.3 8594.3 No OFA 14

Emissions
0.3 8611.1 No OFA 15

0.3 8615.1 No OFA 17

0.3 8605.0 No OFA 17

0.3 8609.6 No OFA 18

0.3 8610.7 No OFA 18

0.3 8604.1 No OFA 20

0.3 8614.4 No OFA 20

0.3 8601.7 No OFA 21

0.3 8608.4 No OFA 16

0.3 8608.7 No OFA 31

0.3 8621.7 No OFA 20

0.3 8605.9 No OFA 45

0.3 8607.9 No OFA 34

0.3 8606.4 No OFA 16

0.3 8603.8 No OFA 13

0.3 8607.8 No OFA 10

0.3 8599.3 No OFA 12

0.3 8621.1 No OFA 11

0.3 8597.5 No OFA 10

0.3 8619.6 No OFA 10

0.4 8602.8 No OFA 13

0.4 8609.7 No OFA 13

0.4 8613.6 No OFA 15

0.4 8605.5 No OFA 16

0.4 8609.7 No OFA 17

0.4 8601.0 No OFA 15

0.4 8614.0 No OFA 16

0.4 8602.5 No OFA 15

0.4 8617.2 No OFA 18

0.4 8607.3 No OFA 17

0.4 8609.6 No OFA 19

0.4 8390.1 No OFA8

0.4 8491.3 No OFA 28

0.4 8558.8 No OFA 27

0.5 8582.4 No OFA 29

0.5 8592.2 No OFA8

0.5 8576.8 No OFA5

0.5 8610.8 No OFA7

0.5 8559.9 No OFA 11

0.5 8600.3 No OFA 21

0.5 8601.6 No OFA 17

0.5 8606.4 No OFA 20

14.0 8624.3 No OFA 21

39.4 8622.0 2/3 OFA - Throttled 75

55.5 8617.8 2/3 OFA - Open 60

63.8 8605.7 2/3 OFA - Open 50

63.8 8608.4 2/3 OFA - Open 50

63.8 8609.8 2/3 OFA - Open 51

63.8 8606.7 2/3 OFA - Open 51

63.8 8619.5 2/3 OFA - Open 51

63.8 8615.0 2/3 OFA - Open 53

63.8 8620.6 2/3 OFA - Open 54
63.9 8609.1 2/3 OFA - Open 56

63.9 8619.8 2/3 OFA - Open 53

63.9 8617.9 2/3 OFA - Open 55

63.9 8608.6 2/3 OFA - Open 52

63.9 8607.5 2/3 OFA - Open 49

63.9 8612.6 2/3 OFA - Open 44

63.9 8613.6 2/3 OFA - Open 45

63.9 8604.0 2/3 OFA - Open 44

64.0 8619.1 2/3 OFA - Open 45
1SGBFT0155

1SGBFT0156

1SGBFT0157

1SGBFT0158

1SGAPE0049

CO (lb/hr)

Hourly 

Rate Tons/mo

Average 

Hourly

164.40 160.44 31.35 104.37

152.64 159.97 104.40

129.64 153.21 104.42

142.17 147.21 104.43

168.99 148.36 31.43 104.45

122.63 140.86 104.47

105.09 134.72 104.48

82.40 119.78 104.49

90.35 100.12 31.48 104.49

88.79 91.66 104.48

82.72 86.07 104.47

40.94 75.70 104.46

24.37 59.21 31.50 104.44

12.48 40.13 104.41

15.63 23.36 104.38

32.14 21.15 104.35

64.18 31.11 31.52 104.32

97.61 52.39 104.29

79.96 68.47 104.28

82.79 81.14 104.27

94.42 88.70 31.56 104.26

85.71 85.72 104.26

86.31 87.31 104.25

82.88 87.33 104.24

89.86 86.19 31.61 104.23

89.21 87.07 104.23

85.84 86.95 104.22

88.53 88.36 104.21

93.60 89.29 31.65 104.21

91.96 89.98 104.20

103.81 94.47 104.20

117.84 101.80 104.20

123.75 109.34 31.71 104.20

108.72 113.53 104.20

97.94 112.06 104.21

Emissions
109.33 109.94 104.21

120.64 109.16 31.76 104.21

123.05 112.74 104.21

130.06 120.77 104.22

126.83 125.15 104.23

139.93 129.97 31.83 104.24

140.10 134.23 104.25

149.74 139.15 104.27

112.08 135.46 104.28

217.59 154.88 31.90 104.30

143.74 155.79 104.32

313.97 196.85 104.36

237.92 228.30 104.41

116.45 203.02 32.01 104.45

93.58 190.48 104.49

70.72 129.67 104.50

84.41 91.29 104.49

80.30 82.25 32.05 104.48

72.39 76.95 104.47

71.32 77.10 104.46

89.24 78.31 104.45

90.67 80.91 32.09 104.44

104.79 89.01 104.43

115.30 100.00 104.43

122.83 108.40 104.43

106.14 112.26 32.14 104.44

116.53 115.20 104.44

108.77 113.57 104.44

124.04 113.87 104.45

118.67 117.00 32.20 104.45

130.66 120.54 104.46

56.49 107.47 104.46

194.72 125.14 104.47

186.54 142.10 32.27 104.48

203.68 160.36 104.51

57.65 160.65 104.53

39.13 121.75 104.54

50.81 87.82 32.32 104.53

78.89 56.62 104.51

144.70 78.38 104.50

118.44 98.21 104.50

139.86 120.47 32.38 104.50

147.44 137.61 104.52

527.24 233.24 104.57

420.09 308.66 104.65

354.05 362.20 32.56 104.76

353.55 413.73 104.88

358.44 371.53 104.99

364.94 357.74 105.09

365.18 360.52 32.74 105.19

374.76 365.83 105.30

380.77 371.41 105.40
396.97 379.42 105.51

378.96 382.87 32.93 105.63

388.22 386.23 105.74

366.74 382.72 105.85

345.25 369.79 105.96

317.31 354.38 33.11 106.06

320.03 337.33 106.15

311.71 323.58 106.24

322.92 317.99 106.32
CO Emissions Analysis: O2 vs. Damper Position

OFA Portion to Total Airflow (%) 2COAXI172B

Hour of Operation: 693.25 Inlet Damper Positions (%open)

Tons of CO 27.41 SW Damper 2SGBKS0169

Average Hourly Rate79.07 SE Damper 2SGBKS0170

Data Repl. Ratio (%) NW Damper 2SGBKS0171

System Shut Down 4.132 NE Damper 2SGBKS0172

Substitute Data 0.000

East Side O2 2COAXI079A

Start Time Interval East Side O2 2SGAAZ0050

9/1/06 0:00 0:15:00

Run Date Period East Side West Side

Boiler Excess 

O2%

9/27/06 0:00 3.49 3.64 3.57

9/27/06 0:15 3.46 3.81 3.66

9/27/06 0:30 3.17 4.04 3.65

9/27/06 0:45 3.33 3.97 3.69

9/27/06 1:00 3.10 4.20 3.71

9/27/06 1:15 3.43 4.26 3.88

9/27/06 1:30 3.90 4.33 4.13

9/27/06 1:45 3.75 4.36 4.08

9/27/06 2:00 3.91 4.22 4.08

9/27/06 2:15 4.20 4.69 4.46

9/27/06 2:30 4.34 4.76 4.56

9/27/06 2:45 4.35 4.69 4.53

9/27/06 3:00 4.28 4.46 4.37

9/27/06 3:15 5.08 4.88 4.97

9/27/06 3:30 5.31 5.06 5.18

9/27/06 3:45 4.93 4.74 4.83

9/27/06 4:00 5.11 4.91 5.00

9/27/06 4:15 5.57 5.59 5.58

9/27/06 4:30 6.09 5.85 5.96

9/27/06 4:45 6.12 5.82 5.96

9/27/06 5:00 6.14 5.79 5.95

9/27/06 5:15 5.15 4.97 5.05

9/27/06 5:30 4.61 4.49 4.55

9/27/06 5:45 4.70 4.60 4.65

9/27/06 6:00 4.81 4.38 4.58

9/27/06 6:15 4.60 4.09 4.33

9/27/06 6:30 3.92 3.62 3.77

9/27/06 6:45 3.60 3.06 3.32

9/27/06 7:00 3.40 2.72 3.04

9/27/06 7:15 3.12 2.60 2.85

9/27/06 7:30 2.82 2.90 2.87

9/27/06 7:45 2.68 3.05 2.89

9/27/06 8:00 2.73 3.01 2.89

9/27/06 8:15 2.66 3.04 2.88

9/27/06 8:30 2.48 3.12 2.85

COMPLIANCE CALCULATION

Unit 2 PI Tags

O2 Values
9/27/06 8:45 2.41 3.10 2.79

9/27/06 9:00 2.49 3.20 2.89

9/27/06 9:15 2.46 3.15 2.84

9/27/06 9:30 2.52 3.22 2.90

9/27/06 9:45 2.47 3.13 2.84

9/27/06 10:00 2.50 3.19 2.88

9/27/06 10:15 2.50 3.25 2.91

9/27/06 10:30 2.47 3.18 2.87

9/27/06 10:45 2.48 3.16 2.85

9/27/06 11:00 2.37 3.21 2.83

9/27/06 11:15 2.41 3.26 2.88

9/27/06 11:30 2.42 3.23 2.87

9/27/06 11:45 2.56 3.12 2.86

9/27/06 12:00 2.42 3.17 2.83

9/27/06 12:15 2.56 3.19 2.92

9/27/06 12:30 2.37 3.22 2.84

9/27/06 12:45 2.26 3.26 2.81

9/27/06 13:00 2.41 3.21 2.85

9/27/06 13:15 2.50 3.15 2.86

9/27/06 13:30 2.58 3.13 2.88

9/27/06 13:45 2.77 2.98 2.88

9/27/06 14:00 2.65 2.94 2.82

9/27/06 14:15 2.91 2.89 2.89

9/27/06 14:30 2.77 3.09 2.94

9/27/06 14:45 2.48 3.05 2.79

9/27/06 15:00 2.53 3.09 2.83

9/27/06 15:15 2.70 3.19 2.96

9/27/06 15:30 2.62 3.17 2.92

9/27/06 15:45 2.45 3.17 2.84

9/27/06 16:00 2.40 3.19 2.83

9/27/06 16:15 2.60 3.21 2.93

9/27/06 16:30 2.46 3.21 2.87

9/27/06 16:45 2.52 3.19 2.88

9/27/06 17:00 2.53 3.19 2.88

9/27/06 17:15 2.51 3.19 2.88

9/27/06 17:30 2.49 3.18 2.86

9/27/06 17:45 2.52 3.18 2.88

9/27/06 18:00 2.66 3.17 2.93

9/27/06 18:15 2.47 3.22 2.87

9/27/06 18:30 2.41 3.29 2.88

9/27/06 18:45 2.53 3.32 2.95

9/27/06 19:00 2.28 3.30 2.82

9/27/06 19:15 2.32 3.20 2.79

9/27/06 19:30 2.40 3.37 2.92

9/27/06 19:45 2.42 3.35 2.93

9/27/06 20:00 2.27 3.34 2.84

9/27/06 20:15 2.40 3.31 2.89

9/27/06 20:30 2.48 3.49 3.03

9/27/06 20:45 2.40 3.31 2.89

9/27/06 21:00 2.26 3.32 2.85

9/27/06 21:15 2.38 3.24 2.84

9/27/06 21:30 2.36 3.32 2.88
9/27/06 21:45 2.33 3.24 2.82

9/27/06 22:00 2.46 3.24 2.88

9/27/06 22:15 2.45 3.26 2.88

9/27/06 22:30 2.48 3.22 2.88

9/27/06 22:45 2.51 3.26 2.92

9/27/06 23:00 2.41 3.31 2.89

9/27/06 23:15 2.62 3.12 2.89

9/27/06 23:30 2.62 3.06 2.86

9/27/06 23:45 2.58 3.14 2.88
OFA Total Flow (kpph) 2COAXI172C

1/3 Port Damper Positions (%open)

SW Damper 2SGBKS0177

SE Damper 2SGBKS0178

NW Damper 2SGBKS0179

NE Damper 2SGBKS0180

West Side O2 2COAXI080A

West Side O2 2SGAAZ0051

OFA Portioned 

Flow (% of total) Total OFA Flow Plenum Inlet 1/3 Port

1.1 83.15 74.0 0.5

1.1 79.78 74.0 0.5

1.1 79.15 74.0 0.5

1.6 122.41 74.0 0.5

1.6 120.87 74.0 0.5

1.1 74.17 74.0 0.5

1.1 68.36 74.0 0.6

1.0 67.31 74.0 0.6

1.0 66.30 74.0 0.6

1.1 70.92 74.0 0.6

1.0 61.14 74.1 0.6

1.1 63.73 74.1 0.6

1.2 68.43 74.1 0.6

1.2 63.32 74.1 0.6

1.1 57.12 74.1 0.6

1.1 56.82 74.1 0.6

1.1 56.16 74.1 0.6

1.1 54.35 74.1 0.6

1.1 53.33 74.1 0.6

1.1 52.15 74.1 0.6

1.1 54.87 74.1 0.6

1.1 55.60 74.1 0.6

1.1 57.80 74.1 0.6

1.1 59.48 74.1 0.6

1.1 61.86 74.1 0.6

1.1 66.50 74.2 0.6

1.1 63.36 74.2 0.6

1.0 62.99 74.2 0.6

1.0 68.11 74.2 0.6

1.0 75.06 74.2 0.7

1.2 94.58 74.2 0.7

1.5 114.41 74.2 0.7

1.5 117.53 74.2 0.6

1.6 118.42 74.2 0.6

1.6 119.15 74.2 0.6

OFA Operating Status
1.4 109.72 74.2 0.6

1.4 106.40 74.2 0.6

1.4 110.81 74.2 0.6

1.6 117.44 74.2 0.6

1.6 119.53 74.2 0.6

1.6 122.47 74.2 0.6

1.6 124.95 74.2 0.6

1.6 127.60 74.2 0.6

1.6 128.49 74.2 0.6

1.6 130.55 74.1 0.6

1.5 132.31 74.1 0.6

1.5 133.20 74.1 0.6

1.5 134.30 74.1 0.6

1.5 133.29 74.1 0.6

1.5 135.04 74.1 0.6

1.5 134.60 74.1 0.5

1.3 86.98 74.1 0.5

1.3 95.91 74.1 0.5

1.5 115.74 74.0 0.5

1.4 118.04 74.0 0.5

1.6 120.40 74.0 0.5

1.6 121.34 74.0 0.5

1.6 121.92 74.0 0.5

1.6 123.95 74.0 0.5

1.6 123.35 74.0 0.5

1.6 125.31 74.0 0.5

1.6 122.46 74.0 0.5

1.6 120.70 74.0 0.5

1.6 121.89 73.9 0.5

1.7 122.81 73.9 0.5

1.7 123.08 73.9 0.5

1.7 123.86 73.9 0.5

1.3 86.39 73.9 0.5

1.1 75.34 73.9 0.5

1.1 74.34 73.9 0.5

1.1 73.67 73.9 0.5

1.1 72.71 73.9 0.5

1.1 73.04 73.9 0.5

1.1 72.84 73.9 0.5

1.1 73.40 73.9 0.5

1.0 73.36 73.9 0.5

1.0 73.31 73.9 0.5

1.0 73.28 73.9 0.5

1.0 74.42 73.9 0.5

1.0 74.57 73.9 0.5

1.0 73.83 73.9 0.5

1.0 74.06 73.9 0.5

1.0 74.18 73.9 0.5

1.2 86.29 73.9 0.5

1.2 86.21 73.9 0.5

1.2 86.94 73.9 0.5

1.1 76.44 74.0 0.5
1.0 73.97 74.0 0.5

1.1 72.92 74.0 0.5

1.1 73.32 74.0 0.5

1.1 73.18 74.0 0.5

1.2 73.18 74.0 0.6

1.2 73.15 74.0 0.6

1.3 73.44 74.0 0.6

1.3 73.71 74.0 0.6

1.3 73.45 74.0 0.6
2/3 Port Damper Positions (%open) Partitioned Flow (kpph)

SW Damper 2SGBKS0173 SW Ports

SE Damper 2SGBKS0174 SE Ports

NW Damper 2SGBKS0175 NW Ports

NE Damper 2SGBKS0176 NE Ports

Average Excess O2 2COAXI187A Heat Input

Average Excess O2 (Post-Outage)

Boiler Data

2/3 Port Heat Input OFA Condition CO (ppm)

1.3 8283.19 No OFA 3

1.3 7955.73 No OFA 2

1.3 7945.66 No OFA 2

1.3 7947.29 No OFA 2

1.3 7929.54 No OFA 2

1.3 7500.22 No OFA 1

1.3 7130.77 No OFA 1

1.3 7126.28 No OFA 1

1.4 7048.69 No OFA 1

1.4 6524.96 No OFA 0

1.4 6311.59 No OFA 0

1.4 6309.30 No OFA 0

1.4 6374.24 No OFA 1

1.4 5950.65 No OFA 0

1.4 5525.16 No OFA 0

1.4 5529.83 No OFA 0

1.4 5433.47 No OFA 0

1.4 4906.24 No OFA 0

1.4 4679.67 No OFA 0

1.4 4671.51 No OFA 0

1.4 4774.75 No OFA 0

1.4 5341.37 No OFA 0

1.4 5851.77 No OFA 0

1.4 5899.63 No OFA 0

1.4 6186.50 No OFA 0

1.4 6795.31 No OFA 1

1.4 7126.70 No OFA 2

1.4 7366.17 No OFA 5

1.4 7962.47 No OFA 9

1.4 8341.76 No OFA 15

1.4 8353.67 No OFA 14

1.4 8353.27 No OFA 14

1.4 8350.90 No OFA 14

1.4 8350.49 No OFA 14

1.3 8353.95 No OFA 15

Emissions
1.3 8349.21 No OFA 18

1.3 8350.71 No OFA 14

1.3 8353.36 No OFA 15

1.3 8348.03 No OFA 13

1.3 8352.00 No OFA 15

1.3 8350.93 No OFA 14

1.3 8354.50 No OFA 13

1.3 8351.09 No OFA 14

1.3 8350.41 No OFA 15

1.3 8351.52 No OFA 16

1.3 8351.05 No OFA 14

1.3 8353.78 No OFA 14

1.3 8350.35 No OFA 15

1.2 8348.41 No OFA 16

1.2 8350.45 No OFA 13

1.2 8348.40 No OFA 16

1.2 8352.50 No OFA 17

1.2 8350.98 No OFA 15

1.2 8348.66 No OFA 15

1.2 8353.73 No OFA 14

1.2 8346.90 No OFA 14

1.2 8353.75 No OFA 16

1.2 8351.38 No OFA 14

1.2 8345.87 No OFA 12

1.2 8356.78 No OFA 18

1.2 8348.69 No OFA 16

1.2 8350.87 No OFA 11

1.2 8355.38 No OFA 13

1.2 8353.88 No OFA 15

1.1 8349.73 No OFA 16

1.1 8347.68 No OFA 12

1.1 8350.34 No OFA 14

1.1 8353.64 No OFA 14

1.1 8352.95 No OFA 14

1.1 8351.73 No OFA 14

1.1 8354.17 No OFA 15

1.1 8350.35 No OFA 14

1.1 8348.52 No OFA 12

1.1 8351.05 No OFA 14

1.1 8350.12 No OFA 14

1.1 8350.39 No OFA 12

1.1 8352.12 No OFA 16

1.1 8349.55 No OFA 18

1.1 8352.13 No OFA 13

1.1 8347.33 No OFA 12

1.1 8351.79 No OFA 15

1.1 8351.96 No OFA 14

1.1 8331.63 No OFA9

1.1 8332.29 No OFA 14

1.1 8333.38 No OFA 15

1.1 8333.99 No OFA 15

1.1 8333.46 No OFA 14
1.1 8337.47 No OFA 16

1.1 8333.86 No OFA 14

1.0 8331.24 No OFA 14

1.0 8330.99 No OFA 14

1.0 8327.70 No OFA 13

1.0 8333.77 No OFA 14

1.1 8328.54 No OFA 14

1.1 8330.98 No OFA 15

1.1 8331.64 No OFA 14
NEW DCS E/W O2 Tags

2SGAAZ0048E

2SGAAZ0048W

2SGAAZ0050E

2SGBFT0155 2SGAAZ0050W

2SGBFT0156 2SGAAZ0052E

2SGBFT0157 2SGAAZ0052W

2SGBFT0158

%OFA Flow

2SGAPE0049 2SGBPETOFA

CO (lb/hr) Average Hourly Tons/mo

19.07 21.03 23.87 76.52

15.18 19.77 76.50

15.46 18.39 76.48

14.36 16.02 76.45

13.80 14.70 23.88 76.43

9.26 13.22 76.40

5.49 10.73 76.38

6.07 8.65 76.35

5.99 6.70 23.88 76.32

2.88 5.11 76.29

2.35 4.32 76.27

2.46 3.42 76.24

3.24 2.73 23.88 76.21

1.17 2.31 76.18

0.80 1.92 76.15

1.34 1.64 76.12

1.02 1.08 23.88 76.09

0.41 0.89 76.06

0.24 0.76 76.03

0.24 0.48 76.00

0.25 0.29 23.88 75.97

0.93 0.42 75.94

2.22 0.91 75.91

1.90 1.32 75.88

2.22 1.82 23.88 75.85

3.74 2.52 75.82

10.99 4.71 75.79

29.43 11.59 75.77

60.99 26.29 23.89 75.75

103.85 51.31 75.74

98.84 73.28 75.74

93.28 89.24 75.74

93.19 97.29 23.94 75.75

96.60 95.48 75.76

104.71 96.95 75.77

Emissions
123.47 104.49 75.78

94.61 104.85 24.00 75.79

105.79 107.14 75.80

90.50 103.59 75.81

105.98 99.22 75.82

96.01 99.57 24.05 75.83

88.78 95.32 75.84

98.49 97.32 75.85

104.72 97.00 75.86

109.39 100.34 24.10 75.87

95.51 102.03 75.88

97.52 101.78 75.89

101.15 100.89 75.90

109.54 100.93 24.15 75.91

87.55 98.94 75.91

106.58 101.21 75.92

115.30 104.74 75.94

105.05 103.62 24.20 75.95

100.96 106.97 75.96

94.95 104.06 75.97

94.90 98.96 75.98

113.03 100.96 24.25 75.99

93.15 99.01 76.00

83.00 96.02 76.01

122.43 102.90 76.02

108.73 101.82 24.30 76.03

78.38 98.13 76.03

86.26 98.95 76.04

106.30 94.92 76.05

109.98 95.23 24.35 76.06

84.51 96.76 76.07

99.37 100.04 76.08

96.96 97.70 76.08

96.09 94.23 24.39 76.09

95.50 96.98 76.10

101.09 97.41 76.11

95.48 97.04 76.12

83.74 93.95 24.44 76.12

97.70 94.50 76.13

96.12 93.26 76.14

80.58 89.53 76.14

111.20 96.40 24.49 76.15

120.41 102.08 76.16

86.43 99.65 76.17

84.62 100.67 76.18

105.85 99.33 24.54 76.19

93.95 92.71 76.19

65.55 87.49 76.20

93.93 89.82 76.20

104.96 89.60 24.58 76.21

105.66 92.53 76.22

96.20 100.19 76.22
111.05 104.47 76.24

95.04 101.99 24.63 76.25

95.35 99.41 76.25

94.94 99.09 76.26

87.44 93.19 76.27

93.62 92.84 24.68 76.28

92.77 92.19 76.28

100.61 93.61 76.29

96.74 95.94 76.30
UNIT ONE

OFA Operating Condition n a

No OFA 47259 -7.6817

1/3 OFA 66265 -7.9824

2/3 OFA - Throttled 4029.2 -4.0112

2/3 OFA - Open 1372.4 -3.0919

CALCULATIONS: (for CO in ppm)

CALCULATIONS: (for CO in lb/hr)

Factors

Formula Data Chart

[Cppmvd] = n * (O2%)a 

Where:

[Cppmvd] = concentration of CO in parts per million volume dry

n = curve specific factor obtained from the table below

O2% = percent O2 measured at the boiler exit 

a = curve specific exponent obtained from the table below

Values for n and a factors

 Position

n a

No OFA

47259 -7.6817

1/3 OFA

66265 -7.9824

2/3 OFA - throttled

4029.2 -4.0112

2/3 OFA - full open

1372.4 -3.0919

[Clb/hr] = [Cppmvd] * 2.59 * 10-9 * MW * Fd * 20.9/(20.9-O2%) * HI

where:

[Clb/hr] = pound per hour emission rate

[Cppmvd] = hourly average of CO emissions in parts per million

2.59*10-9 = conversion factor for pound per standard cubic feet

MW = molecular weight of CO

Fd= F factor to convert standard cubic feet per million Btu heat input. 

O2% = hourly average of excess combustion oxygen, in percent

HI = heat input, in million Btu per hour
ASSUMPTIONS:

OFA not in service until OFA portion flow is greater than 5%.

2/3 Damper is considered throttled at 20% to 50%.

2/3 Damper is considered open at greater than 50%.

1/3 damper is open at greater than 20%

MISSING DATA RE_FILL PROTOCOL FOR CO

TABLE 1 - MISSING DATA PROCEDURE FOR SO2 CEMS, CO

DILUENT (CO2 OR O2) MONITORS FOR HEAT INPUT DETERMINATION

Trigger conditions

Monitor data availability Duration (N) of

(percent) CEMS outage

(hours)2

 95 or more . . . . . . . . . . . . . . . N ≤ 24 Average . . . . . . . . . . . . . . . . . . . . . . . . . . 

 N > 24 For SO2, CO2

 Average . . . . . . . . . . . . . . . . . . . . . . . . .

 90th percentile . . . . . . . . . . . . . . . . . . . .

 For O2 and H

 Average . . . . . . . . . . . . . . . . . . . . . . . . .

 10th percentile . . . . . . . . . . . . . . . . . . . .

 90 or more, but below 95 . . . . . N ≤ 8 Average . . . . . . . . . . . . . . . . . . . . . . . . . . 

 N > 8 For SO2, CO2

 Average . . . . . . . . . . . . . . . . . . . . . . . . .

 95th percentile . . . . . . . . . . . . . . . . . . . .

 For O2 and H

 Average . . . . . . . . . . . . . . . . . . . . . . . . .

 5th percentile . . . . . . . . . . . . . . . . . . . . .

 80 or more, but below 90 . . . . . N > 0 For SO2, CO2

 Maximum Value 

 For O2 and H

 Minimum Value 

 Below 80 . . . . . . . . . . . . . . . . N > 0 Maximum potential concentration or % (for

 SO2, CO2, and H

[Clb/hr] = pound per hour emission rate

[Cppmvd] = hourly average of CO emissions in parts per million

2.59*10-9 = conversion factor for pound per standard cubic feet

MW = molecular weight of CO

Fd= F factor to convert standard cubic feet per million Btu heat input. 

O2% = hourly average of excess combustion oxygen, in percent

HI = heat input, in million Btu per hour
UNIT TWO

OFA Operating Condition n a

No OFA 47259 -7.6817

1/3 OFA 66265 -7.9824

2/3 OFA - Throttled 4029.2 -4.0112

2/3 OFA - Open 1372.4 -3.0919

Formula Data Chart

Factors

CO in parts per million volume dry

tained from the table below

d at the boiler exit 

 obtained from the table below

a

-7.6817

-7.9824

-4.0112

-3.0919

0-9 * MW * Fd * 20.9/(20.9-O2%) * HI

ission rate

f CO emissions in parts per million

or for pound per standard cubic feet

CO

dard cubic feet per million Btu heat input. 

cess combustion oxygen, in percent

Btu per hour
 CEMS, CO2

 CEMS, MOISTURE CEMS AND

 FOR HEAT INPUT DETERMINATION

Calculation routines

Lookback

Method period

 Average . . . . . . . . . . . . . . . . . . . . . . . . . . HB/HA

2

, and H2O**, the greater of: . 

 Average . . . . . . . . . . . . . . . . . . . . . . . . . HB/HA

 90th percentile . . . . . . . . . . . . . . . . . . . . 720 hours

 and H2O

x

, the lesser of: . 

 Average . . . . . . . . . . . . . . . . . . . . . . . . . HB/HA

 10th percentile . . . . . . . . . . . . . . . . . . . . 720 hours

 Average . . . . . . . . . . . . . . . . . . . . . . . . . . HB/HA

2

, and H2O**, the greater of: . 

 Average . . . . . . . . . . . . . . . . . . . . . . . . . HB/HA

 95th percentile . . . . . . . . . . . . . . . . . . . . 720 hours

 and H2O

x

, the lesser of: . 

 Average . . . . . . . . . . . . . . . . . . . . . . . . . HB/HA

 5th percentile . . . . . . . . . . . . . . . . . . . . . 720 hours

2

, and H2O**, 

 Maximum Value 1 . . . . . . . . . . . . . . . . . . 720 hours

 and H2O

x: 

. 

 Minimum Value 1 . . . . . . . . . . . . . . . . . . . 720 hours

 Maximum potential concentration or % (for

, and H2O**) or .

ission rate

f CO emissions in parts per million

or for pound per standard cubic feet

CO

dard cubic feet per million Btu heat input. 

cess combustion oxygen, in percent

Btu per hour