EMISSIONS TEST REPORT 

POLK POWER STATION 

FACILITY ID NUMBER: 1050233 

EMISSION UNIT ID NO: -001 

UNIT 1 

SYNTHETIC GAS 

CARBON MONOXIDE, VOLATILE ORGANIC COMPOUNDS, 

SULFURIC ACID MIST, VISIBLE EMISSIONS EVALUATION, and 

OXIDES OF NITROGEN, SULFUR DIOXIDE FROM CEMS 

December 15 & 16, 2008 

Prepared For: 

Tampa Electric Company 

Polk Power Station 

P.O. Box 111 

Tampa, Florida 33601-0111 

Prepared By: 

Tampa Electric Company 

Environmental, Health, & Safety 

Air Services Group 

Environmental, Health, & Safety 

Air Services Group 

5010 Causeway Boulevard 

Tampa, Florida 33619- 6130 
REPORT CERTIFICATION 

 The sampling and subsequent data entry/reduction detailed in this report 

was conducted at my direction, and I hereby certify that this test report is 

authentic and accurate to the best of my knowledge. 

Signature:__________________________ 

Jorge A. Varino 

Environmental Technician 

Test Team Lead 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the test performance, associated quality assurance 

activities, the resultant calculations, and the contents of this report, and certify 

that all project quality objectives have been met. This report is approved for 

submittal. 

Signature:__________________________ 

Raymond A. McDarby, Jr. 

Senior Environmental Technician 

Quality Assurance/Quality Control Specialist 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the testing details and results submitted in this report, 

and hereby certify that this test report is authentic and accurate to the best of 

my knowledge. 

Signature:__________________________ 

David A. Smith, QSTI 

Coordinator – Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 
TABLE OF CONTENTS

SECTION PAGE NO.

1.0 INTRODUCTION 1 

2.0 DISCUSSION OF RESULTS 2 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES 4 

4.0 TABULATED RESULTS 

CARBON MONOXIDE TEST DATA 6 

VOLATILE ORGANIC COMPOUND DATA 7 

SULFURIC ACID MIST TEST DATA 8 

NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 9 

HEAT INPUT CALCULATIONS, DECEMBER 15, 2008 10 

HEAT INPUT CALCULATIONS, DECEMBER 16, 2008 11 

5.0 STACK SAMPLING LOCATION DIAGRAM 13 

APPENDICES

A. CARBON MONOXIDE TEST INFORMATION

SUMMARIZED RUN DATA & QA/QC 

TEST RUN LOG 

CYLINDER GAS CERTIFICATES 

B. VOLATILE ORGANIC COMPOUNDS TEST DATA

 FIELD DATA SHEETS 

 LABORATORY ANALYSIS – ENTHALPY ANALYTICAL, INC. 

C. SULFURIC ACID MIST TEST DATA

 FIELD DATA SHEETS 

 CALCULATED RUN DATA 

 LABORATORY ANALYSIS 

 EQUIPMENT CALIBRATIONS 

D. TURBINE DATA

E. FUEL ANALYSIS

F. CEMS DATA

G. VISIBLE EMISSION DATA SHEET

H. TEST PARTICIPANTS
1 

1.0 INTRODUCTION

On December 15, and 16, 2008, Tampa Electric Company’s, Environmental Services, 

Air Services Group performed source emission tests, on Unit No. 1 at the Polk Power 

Station. The tests include Carbon Monoxide (CO), Volatile Organic Compounds 

(VOCs), Sulfuric Acid Mist (SAM), and Visible Emissions Observations (VEOs). Unit 

No. 1 is a combined cycle combustion turbine generating unit. The combustion turbine 

was fired with syngas from the solid fuel gasification system. A blend of petroleum coke 

and bituminous coal was gasified for this test. Testing was conducted according to 

United States Environmental Protection Agency (USEPA) test methods stipulated in 40 

CFR Part 60, Appendix A and Florida Department of Environmental Protection (FDEP) 

Permit No. 1050233-016-AV. 

Nitrogen Oxides (NOx) and Sulfur Dioxide (SO2) data was taken from the Continuous 

Emissions Monitoring System’s (CEMS) Data Acquisition and Handling System (DAHS) 

concurrent with the SAM testing, and is presented as averages over the test period. 
2 

2.0 DISCUSSION OF RESULTS

Executive Summary 

Tampa Electric Company 

Polk Power Station 

General Electric 7F Combined Cycle Combustion Turbine 

Emission Unit ID -001 

Solid Fuel Derived Synthetic Gas 

Compliance Parameter Test Result FDEP Permit Limit 

CO, ppmvd @15% O2 3 25 

CO, lbs/hr 12 98 

VOC, lbs/hr 41 3 

SAM, lbs/hr 43 55 

VE, % opacity 0 10 

December 15, 2008 

NOX, lbs/hr 106.30 220.25 

SO2, lbs/hr 315 357 

Heat Input, mmBtu/hr 1638 -- 

Maximum Heat Input 1 1751 -- 

Unit Load (% of permit) 2 94% 90 – 100% 

December 16, 2005 

NOX, lbs/hr 103.59 220.25 

SO2, lbs/hr 319 357 

Heat Input, mmBtu/hr 1629 

Maximum Heat Input 1 1752 

Unit Load (% of permit) 2 93% 90 – 100% 

1Maximum Heat Input is Permitted Maximum Heat Input Rate, 1755 mmBtu/hr @ 59o F, 

Corrected to Average Ambient Temperature Recorded During the Test Period. 

2Unit Load (% of permit) is Heat Input Divided by Maximum Heat Input times 100. 

The Carbon Monoxide (CO) concentration and emission rate was derived from three 1-

hour Reference Method 10 test runs conducted on December 15, 2008. The calculated 

average CO concentration was 3 ppmvd @ 15% O2. The calculated average emission 

rate was 12 lbs/hr. The FDEP permitted concentration is 25 ppmvd @15% O2. The 

FDEP permitted emission rate is 98 lbs/hr based on a 30-day rolling average. 

The Volatile Organic Compounds (VOCs) emission rate was derived from three 1-hour 

Reference Method 18 test runs conducted on December 15, 2008. The calculated 

average VOCs emission rate was 41 lbs/hr. The FDEP permitted emission rate is 3 
3 

lbs/hr based on a 30-day rolling average. 

The Sulfuric Acid Mist (SAM) emission rate was derived from six 1-hour Reference 

Method 8 test runs conducted on December 15 and 16, 2008. The calculated average 

SAM emission rate was 43 lbs/hr. The FDEP permitted emission rate is 55 lbs/hr based 

on a 30-day rolling average. 

The Visible Emissions Observations (VEO) yielded an average opacity of 0% for the 1-

hour test. The FDEP permitted opacity is 10 percent. 

During the SAM testing, the Nitrogen Oxides (NOx) average emission rate was 104.59 

lbs/hr. 

During the SAM testing, the Sulfur Dioxide (SO2) average emission rate was 317 lbs/hr. 

During the December 15th, test Unit No. 1 was operated at an average heat input of 

1638 mmBtu/hr. The FDEP permitted heat input is 1755 mmBtu/hr, at an ambient 

temperature of 59o (corrected to 1751 mmBtu/hr based on an average inlet vane 

temperature of 75o F, and the manufacturer’s heat input correction curve for this unit). 

The unit operated at 94% of permitted capacity. 

During the December 16th, test Unit No. 1 was operated at an average heat input of 

1629 mmBtu/hr. The FDEP permitted heat input is 1755 mmBtu/hr, at an ambient 

temperature of 59o (corrected to 1751 mmBtu/hr based on an average inlet vane 

temperature of 70o F, and the manufacturer’s heat input correction curve for this unit). 

The unit operated at 93% of permitted capacity. 
4 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generating Station is located at County Road 630 approximately 

13 miles southwest of Bartow, Polk County, Florida. Unit No. 1 is a Combined Cycle 

Combustion Turbine generating unit, with a net capacity of 192 MW when fired with 

Syngas fuel. The source sampling location consists of a circular stack 19 feet in 

diameter with four sample ports located 90 degrees apart on the stack circumference. 

A diagram of the stack sampling location is included along with other pertinent 

information on the test site. 

Carbon Monoxide sampling was performed in accordance with USEPA Reference 

Method 10 (40 CFR Part 60, Appendix A) “Determination of Carbon Monoxide 

Emissions From Stationary Sources”. Testing was performed using a Thermo 

Environmental Instruments model 48C Carbon Monoxide Analyzer. 

Volatile Organic Compound sampling was performed in accordance with USEPA 

Reference Method 18 “Measurement of Gaseous Organic Compound Emissions by Gas 

Chromatography”. Analysis was performed by Enthalpy Analytical, Inc. 

Sulfuric Acid Mist sampling was performed in accordance with USEPA Reference 

Method 8 “Determination of Sulfuric Acid Mist and Sulfur Dioxide Emissions From 

Stationary Sources”. 

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. 

This data was taken as 1-minute averages over the time frame consistent with the 

Sulfuric Acid Mist testing. 

Plant operational data was taken from the Plant Information (PI) server system. Data 

captured included the minute average load, minute fuel flow, minute inlet vane 

temperature, and minute saturator readings. 
5 

4.0 TABULATED RESULTS
POLK POWER STATION

CARBON MONOXIDE DATA

CO % O2 CO, ppmvd CO

Run # Start Stop ppmvd volume @ 15% O2 lbs/hr

1 10:56 11:56 5.30 12.08 3.55 12.66

2 12:16 13:16 5.19 12.05 3.46 12.36

3 13:29 14:29 5.05 12.08 3.38 12.06

Averages: 3.461 12.359

CO, ppmvd @ 15% O2 is calculated as:

CO, ppmvd x (5.9 / (20.9 - % O2, volume))

CO, lbs/hr is calculated as:

CO, ppmvd x Cf x Fd x (20.9 / (20.9 - % O2, volume) x Heat Input

where: Cf = 7.27249E-08 lb/scf

Fd = 8460 dscf/mmBtu

Heat Input = 1638 mmBtu/hr

Test Times are Eastern Standard.

Test Times

RM Data Calculated Data

HEAT RECOVERY STEAM GENERATOR

UNIT 1

December 15, 2008

6 
POLK POWER STATION

VOLATILE ORGANIC COMPOUNDS DATA

THC, ppm VOC Flow Rate VOC

Run # Start Stop as C6H14 lb/scf scf/hr lbs/hr

1 10:56 11:56 2.01 4.498E-07 4.890E+07 21.99

2 12:16 13:16 3.54 7.921E-07 4.899E+07 38.81

3 13:29 14:29 5.63 1.260E-06 4.900E+07 61.73

Averages: 40.844

VOC, lb/scf calculated as:

ppm VOC x Cf 

where:

Cf = Mole wieght of hexane (86.18 lb/lb-mole) x 10-6 / (385.15 scf/lb-mole)

2.238E-07 lbs/dscf

VOC, lbs/hr calculated as:

VOC, lb/scf x Stack Flow, scf/hr

Test Times

HEAT RECOVERY STEAM GENERATOR

UNIT 1

December 15, 2008

7 
Environmental 

Air Service

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Summary

Customer: Polk Power StationFacility: Unit 1Sampling Location: StackOperating Conditions: Full LoadTest Date:

Run #1 Run #2 Run #3 Run #4 Run #5 Run #6 A

Gas Flow Rates

Qs, acfm: 1279774.1 1305033.2 1310020.0 1265799.8 1265685.7 1269097.6 

Qs(std), dscfm: 817322.9 834220.4 836935.0 810020.3 810552.2 808202.2 

Sampled Volume, Vm(std), dscf: 36.98 37.66 37.80 36.95 36.57 36.79 

Stack Moisture, Bws x 100, %: 5.98 5.81 5.68 5.56 5.22 5.77 

Isokinetic Sampling Rate, I, %: 101 100.8 100.8 101.8 100.7 101.6 

C H2SO4, lb/dscf: 8.015E-07 1.237E-06 9.791E-07 5.615E-07 7.807E-07 8.102E-07 

E H2SO4, lb/mmBtu: 0.0206 0.0317 0.0251 0.0144 0.0200 0.0208 

E H2SO4, lbs/hr: 39 62 49 27 38 39 

December 15, 2008 December 16, 2008

8 
POLK POWER STATION

NO X & SO 2 COMPLIANCE DATA FROM CEMS

NOx SO2 Flow NOx SO2

ppmvw ppmvw kscfmw lbs/hr lbs/hr

18.21 38.77 814.92 106.30 315

NOx SO2 Flow NOx SO2

ppmvw ppmvw kscfmw lbs/hr lbs/hr

17.78 39.43 813.25 103.59 319

NOX, lbs/hr calculated as:

NOX, ppmvw x 1.194E-07 x Flow, kscfmw x 60 min/hr x 1000/k

SO2, lbs/hr calculated as:

SO2, ppmvw x 1.660E-07 x Flow, kscfmw x 60 min/hr x 1000/k

HEAT RECOVERY STEAM GENERATOR

UNIT 1

December 15, 2008

December 16, 2008

CEM Data Calculated Data

CEM Data Calculated Data

9 
POLK POWER STATION

HEAT INPUT CALCULATION

Average fuel flow: 6626.253 Kcfh

Mole weight correction to meter cal: 0.9883 mole weight correction factor

Corrected fuel flow:1 6548.7258 Kcfh, corrected for density

Average moisture: 2.83 % H20 added to fuel

Corrected fuel flow:2 6363.3492 Kscfh, corrected for moisture

Gross heating value of fuel (HHV): 257.46 Btu/scf

Heat Input: 1638 mmBtu/hr

Average fuel flow from Plant Information Data Base.

Mole weight correction factor to meter calibration is taken from ratio of syngas mole weight

to calibration gas mole weight.

1Average fuel flow times mole weight correction factor.

2Corrected fuel flow times (1 - (Average moisture / 100)).

Gross Heating value of fuel (HHV) is from fuel analysis.

Heat input is (HHV x Corrected fuel flow) / 1000.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

December 15, 2008

10 
POLK POWER STATION

HEAT INPUT CALCULATION

Average fuel flow: 6602.319 Kcfh

Mole weight correction to meter cal: 0.9883 mole weight correction factor

Corrected fuel flow:1 6525.0719 Kcfh, corrected for density

Average moisture: 2.9 % H20 added to fuel

Corrected fuel flow:2 6335.8448 Kscfh, corrected for moisture

Gross heating value of fuel (HHV): 257.15 Btu/scf

Heat Input: 1629 mmBtu/hr

Average fuel flow from Plant Information Data Base.

Mole weight correction factor to meter calibration is taken from ratio of syngas mole weight

to calibration gas mole weight.

1Average fuel flow times mole weight correction factor.

2Corrected fuel flow times (1 - (Average moisture / 100)).

Gross Heating value of fuel (HHV) is from fuel analysis.

Heat input is (HHV x Corrected fuel flow) / 1000.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

December 16, 2008

11 
12 

5.0 SAMPLING LOCATION DIAGRAM
13 

UNFIRED HEAT 

RECOVERY 

BOILER 

TRANSITION 

DUCT 

EXHAUST FROM 

TURBINE 

14 FT. 

38 FT. 

150 FT. 

136 FT. 

POLK POWER STATION

COMBUSTION TURBINE

COMBINED CYCLE UNIT NO.1 

TEST LOCATION 

PORT LOCATION PLAN

19.0 FT.ID. 

STACK DIAMETERS DOWNSTREAM

FROM DISTURBANCE = 2.0 

STACK DIAMETERS UPSTREAM

FROM DISTURBANCE = 0.7 

STACK DIAMETER = 19.0 FT. 

STACK AREA = 283.529 SQ. FT.

STACK AREA =40828.138 SQ. IN. 
APPENDIX A 

CARBON MONOXIDE TEST INFORMATION 
SUMMARIZED RUN DATA & QA/QC 
LabView QA Data

 

Polk Unit 1 Compliance - Report

RUN 1

12/15/2008 10:56:09 11:56:10

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 25 20 10

Units % % PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.6 9.01 3.95

High Level Certified Value (PPM or %) 20.9 18 8.09

Zero Level Observed -0.002 -0.011 0.006

Low Level Observed - - -

Mid Level Observed 10.564 9.001 3.97

High Level Observed 21.023 17.983 8.007

Zero Calibration Error ACE -0.01 -0.06 0.07

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE -0.17 -0.05 0.25

High Level Calibration Error ACE 0.59 -0.09 -1.03

Initial Readings

Zero 0.031 0.039 0.009

Span 10.691 8.887 3.974

Final Readings

Zero 0.095 0.029 -0.019

Span 10.607 8.823 3.964

System Bias (Eq 7E-2)

Initial Zero Bias SB 0.16 0.28 0.04

Initial Span Bias SB 0.61 -0.63 0.05

Final Zero Bias SB 0.46 0.22 -0.31

Final Span Bias SB 0.21 -0.99 -0.07

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.15 0.22 0.11

Initial Span SCE 0.44 -0.68 0.3

Final Zero SCE 0.45 0.16 -0.23

Final Span SCE 0.03 -1.04 0.17

Drift Assessment (Eq 7E-4)

Zero Drift D 0.3 0.06 0.35

Span Drift D 0.4 0.36 0.12

Effluent Gas Concentration (Eq 7E-5)

Raw Results 12.13 8.81 5.33

Corrected Results (ppmv) 12.08 8.96 5.3

Page 1 of 3
LabView QA Data

 

Polk Unit 1 Compliance - Report

RUN 2

12/15/2008 12:16:44 13:16:44

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 25 20 10

Units % % PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.6 9.01 3.95

High Level Certified Value (PPM or %) 20.9 18 8.09

Zero Level Observed -0.002 -0.011 0.006

Low Level Observed - - -

Mid Level Observed 10.564 9.001 3.97

High Level Observed 21.023 17.983 8.007

Zero Calibration Error ACE -0.01 -0.06 0.07

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE -0.17 -0.05 0.25

High Level Calibration Error ACE 0.59 -0.09 -1.03

Initial Readings

Zero 0.095 0.029 -0.019

Span 10.607 8.823 3.964

Final Readings

Zero 0.098 0.034 0.019

Span 10.5 8.837 3.97

System Bias (Eq 7E-2)

Initial Zero Bias SB 0.46 0.22 -0.31

Initial Span Bias SB 0.21 -0.99 -0.07

Final Zero Bias SB 0.48 0.25 0.16

Final Span Bias SB -0.31 -0.91 0

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.45 0.16 -0.23

Initial Span SCE 0.03 -1.04 0.17

Final Zero SCE 0.47 0.19 0.23

Final Span SCE -0.48 -0.96 0.25

Drift Assessment (Eq 7E-4)

Zero Drift D 0.02 0.03 0.47

Span Drift D 0.52 0.08 0.07

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.98 8.79 5.21

Corrected Results (ppmv) 12.05 8.97 5.19

Page 2 of 3
LabView QA Data

 

Polk Unit 1 Compliance - Report

RUN 3

12/15/2008 13:29:24 14:29:25

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 25 20 10

Units % % PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.6 9.01 3.95

High Level Certified Value (PPM or %) 20.9 18 8.09

Zero Level Observed -0.002 -0.011 0.006

Low Level Observed - - -

Mid Level Observed 10.564 9.001 3.97

High Level Observed 21.023 17.983 8.007

Zero Calibration Error ACE -0.01 -0.06 0.07

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE -0.17 -0.05 0.25

High Level Calibration Error ACE 0.59 -0.09 -1.03

Initial Readings

Zero 0.098 0.034 0.019

Span 10.5 8.837 3.97

Final Readings

Zero 0.069 0.036 -0.02

Span 10.52 8.83 3.977

System Bias (Eq 7E-2)

Initial Zero Bias SB 0.48 0.25 0.16

Initial Span Bias SB -0.31 -0.91 0

Final Zero Bias SB 0.34 0.26 -0.32

Final Span Bias SB -0.21 -0.95 0.09

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.47 0.19 0.23

Initial Span SCE -0.48 -0.96 0.25

Final Zero SCE 0.33 0.2 -0.25

Final Span SCE -0.38 -1 0.33

Drift Assessment (Eq 7E-4)

Zero Drift D 0.14 0.01 0.48

Span Drift D 0.1 0.04 0.09

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.97 8.76 5.08

Corrected Results (ppmv) 12.08 8.93 5.05

Page 3 of 3
TEST RUN LOG 
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 7:52:59 AM 20.54 0.02 0.51

12/15/2008 7:53:29 AM 20.54 0.02 0.53

12/15/2008 7:53:59 AM 20.5 0.05 0.36

12/15/2008 7:54:29 AM 20.55 0.09 0.36

12/15/2008 7:54:59 AM 20.63 0.09 0.28

12/15/2008 7:55:29 AM 20.67 0.1 0.32

12/15/2008 7:55:59 AM 20.69 0.1 0.3

12/15/2008 7:56:29 AM 20.7 0.1 0.29

12/15/2008 7:56:59 AM 20.74 0.1 0.31

12/15/2008 7:57:29 AM 20.74 0.1 0.28

12/15/2008 7:57:59 AM 20.74 0.11 0.29

12/15/2008 7:58:29 AM 20.74 0.1 0.31

12/15/2008 7:58:59 AM 20.75 0.1 0.27

12/15/2008 7:59:29 AM 20.76 0.11 0.31

12/15/2008 7:59:59 AM 20.75 0.11 0.28

12/15/2008 8:00:29 AM 21.03 0.11 0.28

12/15/2008 8:00:59 AM 21.05 0.11 0.3

12/15/2008 8:01:29 AM 21.05 0.11 0.3

12/15/2008 8:01:59 AM 21.04 0.11 0.33

12/15/2008 8:02:29 AM 21.05 0.11 0.31

12/15/2008 8:02:59 AM 20.14 0.11 0.3

12/15/2008 8:03:29 AM 20.2 0.11 0.33

12/15/2008 8:03:59 AM 21.05 0.11 0.27

12/15/2008 8:04:29 AM 21.08 0.06 0.22

12/15/2008 8:04:59 AM 21.12 -0.02 0.19

12/15/2008 8:05:29 AM 21.14 -0.03 0.15

12/15/2008 8:05:59 AM 21.15 -0.03 0.17

12/15/2008 8:06:29 AM 21.15 -0.01 0.18

12/15/2008 8:06:59 AM 21.16 -0.01 -0.01

12/15/2008 8:07:29 AM 21.17 -0.01 0.01

12/15/2008 8:07:59 AM Linearity Check 21.17 -0.01 -0.12

12/15/2008 8:08:29 AM Linearity Check 14.1 5.56 -0.46

12/15/2008 8:08:59 AM Linearity Check 10.67 9.44 -0.39

12/15/2008 8:09:29 AM Linearity Check 10.66 9.56 -0.36

12/15/2008 8:09:59 AM Linearity Check 10.66 8.8 -0.37

12/15/2008 8:10:29 AM Linearity Check 10.66 9 -0.38

12/15/2008 8:10:59 AM Linearity Check 10.65 9 -0.26

12/15/2008 8:11:29 AM Linearity Check 20.07 1.15 -0.05

12/15/2008 8:11:59 AM Linearity Check 20.07 0.03 2.85

12/15/2008 8:12:29 AM Linearity Check 20.07 0.27 8.34

12/15/2008 8:12:59 AM Linearity Check 20.07 0.16 4.87

12/15/2008 8:13:29 AM Linearity Check 20.07 0 4.76

12/15/2008 8:13:59 AM Linearity Check 20.07 0 4.73

12/15/2008 8:14:29 AM Linearity Check 20.07 -0.01 3.95

12/15/2008 8:14:59 AM Linearity Check 20.07 2.94 0.68

12/15/2008 8:15:29 AM Linearity Check 20.07 8.33 -0.28

12/15/2008 8:15:59 AM Linearity Check 20.07 8.97 -0.31

12/15/2008 8:16:29 AM Linearity Check 20.07 8.98 -0.29

12/15/2008 8:16:59 AM Linearity Check 10.55 9 -0.3

12/15/2008 8:17:29 AM Linearity Check 10.55 9 -0.31

12/15/2008 8:17:59 AM Linearity Check 12.43 9.77 -0.53

12/15/2008 8:18:29 AM Linearity Check 20.48 16.61 -0.59

12/15/2008 8:18:59 AM Linearity Check 21.02 17.96 -0.57

12/15/2008 8:19:29 AM Linearity Check 21.02 17.98 -0.6

Page 1 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 8:19:59 AM Linearity Check 21.03 17.99 -0.55

12/15/2008 8:20:29 AM Linearity Check 15.8 14.83 -0.31

12/15/2008 8:20:59 AM Linearity Check 10.6 9.28 -0.32

12/15/2008 8:21:29 AM Linearity Check 10.57 9.02 -0.28

12/15/2008 8:21:59 AM Linearity Check 10.56 9.01 -0.11

12/15/2008 8:22:29 AM Linearity Check 3.72 3.99 3.34

12/15/2008 8:22:59 AM Linearity Check 0.01 0.15 3.96

12/15/2008 8:23:29 AM Linearity Check 0 0.02 3.91

12/15/2008 8:23:59 AM Linearity Check 0 0.01 3.97

12/15/2008 8:24:29 AM Linearity Check 0 0.01 3.95

12/15/2008 8:24:59 AM Linearity Check 0 0 4.34

12/15/2008 8:25:29 AM Linearity Check 0 0.03 7.57

12/15/2008 8:25:59 AM Linearity Check 0 0 7.73

12/15/2008 8:26:29 AM Linearity Check 0 0 7.75

12/15/2008 8:26:59 AM Linearity Check 0 0 7.77

12/15/2008 8:27:29 AM Linearity Check 0 0 7.88

12/15/2008 8:27:59 AM Linearity Check 0 0 7.94

12/15/2008 8:28:29 AM Linearity Check 0 0 7.99

12/15/2008 8:28:59 AM Linearity Check 0 0 7.99

12/15/2008 8:29:29 AM Linearity Check 0 -0.01 7.97

12/15/2008 8:29:59 AM Linearity Check 0 -0.01 7.97

12/15/2008 8:30:29 AM Linearity Check 0 0 4.55

12/15/2008 8:30:59 AM Linearity Check 0 -0.01 4.08

12/15/2008 8:31:29 AM Linearity Check 0 -0.01 4.07

12/15/2008 8:31:59 AM Linearity Check 0 -0.01 3.96

12/15/2008 8:32:29 AM Linearity Check 0.01 -0.01 2.3

12/15/2008 8:32:59 AM Linearity Check 20.16 0.05 0.8

12/15/2008 8:33:29 AM Linearity Check 19.21 0.06 0.46

12/15/2008 8:33:59 AM Linearity Check 20.99 0 0.28

12/15/2008 8:34:29 AM Linearity Check 21 -0.01 0.29

12/15/2008 8:34:59 AM - ZERO 21 -0.01 0.29

12/15/2008 8:35:29 AM - ZERO 20.99 -0.01 0.34

12/15/2008 8:35:59 AM - ZERO 20.99 -0.01 -0.03

12/15/2008 8:36:29 AM - ZERO 20.98 -0.01 -0.02

12/15/2008 8:36:59 AM - ZERO 20.98 -0.01 0

12/15/2008 8:37:29 AM - ZERO 20.97 -0.01 -0.01

12/15/2008 8:37:59 AM - ZERO 20.87 0 -0.24

12/15/2008 8:38:29 AM - ZERO 11.25 7.39 -0.31

12/15/2008 8:38:59 AM - ZERO 10.61 8.77 -0.3

12/15/2008 8:39:29 AM - Span 10.58 8.83 -0.28

12/15/2008 8:39:59 AM - Span 10.57 8.85 -0.29

12/15/2008 8:40:29 AM - Span 10.56 8.86 -0.29

12/15/2008 8:40:59 AM - Span 10.64 9.01 -0.27

12/15/2008 8:41:29 AM - Span 10.76 9.01 -0.29

12/15/2008 8:41:59 AM - Span 10.61 9.01 -0.29

12/15/2008 8:42:29 AM - Span 10.67 9.01 0.17

12/15/2008 8:42:59 AM - Span 4.19 4.01 2.66

12/15/2008 8:43:29 AM - Span 0.3 0.19 3.86

12/15/2008 8:43:59 AM - Span 0.26 0.07 3.9

12/15/2008 8:44:29 AM - ZERO 0.18 0.04 3.87

12/15/2008 8:44:59 AM - ZERO 0.13 0.03 3.9

12/15/2008 8:45:29 AM - Span 0.15 0.02 3.91

12/15/2008 8:45:59 AM - ZERO 0.07 0.02 3.89

12/15/2008 8:46:29 AM - ZERO 0.03 0.01 3.93

Page 2 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 8:46:59 AM - ZERO 0.17 0.01 3.89

12/15/2008 8:47:29 AM - ZERO 6.27 0.01 1.13

12/15/2008 8:47:59 AM - ZERO 20.3 0.05 0.12

12/15/2008 8:48:29 AM - ZERO 20.72 0.07 0.16

12/15/2008 8:48:59 AM - ZERO 20.72 0.06 0.11

12/15/2008 8:49:29 AM - ZERO 20.29 0.06 0.13

12/15/2008 8:49:59 AM - ZERO 20.76 0.05 0.13

12/15/2008 8:50:29 AM - ZERO 20.94 0.06 0.1

12/15/2008 8:50:59 AM - ZERO 20.95 0.06 0.12

12/15/2008 8:51:29 AM - ZERO 20.94 0.06 0.12

12/15/2008 8:51:59 AM - ZERO 20.93 0.07 0.11

12/15/2008 8:52:29 AM - ZERO 20.77 0.07 0.14

12/15/2008 8:52:59 AM - ZERO 20.97 0.05 0.08

12/15/2008 8:53:29 AM - ZERO 20.95 0.05 0.13

12/15/2008 8:53:59 AM - ZERO 20.93 0.08 0.11

12/15/2008 8:54:29 AM - ZERO 20.93 0.08 0.12

12/15/2008 8:54:59 AM - ZERO 20.93 0.08 0.14

12/15/2008 8:55:29 AM - ZERO 20.95 0.06 0.12

12/15/2008 8:55:59 AM - ZERO 20.97 0.05 0.1

12/15/2008 8:56:29 AM - ZERO 20.98 0.04 0.12

12/15/2008 8:56:59 AM - ZERO 20.94 0.07 0.13

12/15/2008 8:57:29 AM - ZERO 20.96 0.06 0.11

12/15/2008 8:57:59 AM - ZERO 20.96 0.07 0.15

12/15/2008 8:58:29 AM - ZERO 20.97 0.05 0.14

12/15/2008 8:58:59 AM - ZERO 20.74 0.08 2.81

12/15/2008 8:59:29 AM - ZERO 12.27 7.87 5.55

12/15/2008 8:59:59 AM - ZERO 11.91 8.89 5.64

12/15/2008 9:00:29 AM - ZERO 11.87 8.91 5.72

12/15/2008 9:00:59 AM - ZERO 11.87 8.93 5.56

12/15/2008 9:01:29 AM - ZERO 11.88 8.94 5.4

12/15/2008 9:01:59 AM - ZERO 11.89 8.94 5.44

12/15/2008 9:02:29 AM - ZERO 12.41 8.94 5.49

12/15/2008 9:02:59 AM - ZERO 12.41 8.95 5.51

12/15/2008 9:03:29 AM - ZERO 12.24 8.97 5.54

12/15/2008 9:03:59 AM - ZERO 12.14 8.98 5.56

12/15/2008 9:04:29 AM - ZERO 12.12 8.98 5.51

12/15/2008 9:04:59 AM - ZERO 12.13 8.97 5.66

12/15/2008 9:05:29 AM - ZERO 12.41 8.97 5.59

12/15/2008 9:05:59 AM - ZERO 12.32 8.99 5.04

12/15/2008 9:25:29 AM TRAVERSE1 - 1 11.91 8.98 5.41

12/15/2008 9:25:59 AM TRAVERSE1 - 1 11.91 8.96 5.42

12/15/2008 9:26:29 AM TRAVERSE1 - 1 11.92 8.98 5.49

12/15/2008 9:26:59 AM TRAVERSE1 - 1 11.91 8.97 5.51

12/15/2008 9:27:29 AM TRAVERSE1 - 1 11.9 8.98 5.37

12/15/2008 9:27:59 AM TRAVERSE1 - 1 11.93 8.96 5.36

12/15/2008 9:28:29 AM TRAVERSE1 - 1 11.91 8.96 5.41

12/15/2008 9:28:59 AM TRAVERSE1 - 1 11.91 8.94 5.62

12/15/2008 9:29:29 AM TRAVERSE1 - 1 11.9 8.96 5.64

12/15/2008 9:29:59 AM TRAVERSE1 - 1 11.91 8.97 5.33

12/15/2008 9:30:29 AM TRAVERSE1 - 1 11.95 8.93 5.36

12/15/2008 9:30:59 AM TRAVERSE1 - 1 12.01 8.94 5.27

12/15/2008 9:31:29 AM TRAVERSE1 - 1 12.1 8.94 5.15

12/15/2008 9:31:59 AM TRAVERSE1 - 1 12.12 8.94 5.21

12/15/2008 9:32:29 AM TRAVERSE1 - 1 12.15 8.95 5.29

Page 3 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 9:32:59 AM TRAVERSE1 - 1 12.17 8.95 5.63

12/15/2008 9:33:29 AM TRAVERSE1 - 1 12.17 8.95 5.45

12/15/2008 9:33:59 AM TRAVERSE1 - 1 11.91 8.93 5.45

12/15/2008 9:34:29 AM TRAVERSE1 - 1 12 8.93 5.56

12/15/2008 9:34:59 AM TRAVERSE1 - 1 11.93 8.95 5.51

12/15/2008 9:35:29 AM TRAVERSE1 - 1 11.99 8.94 5.49

12/15/2008 9:35:59 AM TRAVERSE1 - 1 12.01 8.96 5.36

12/15/2008 9:36:29 AM TRAVERSE1 - 1 12.01 8.94 5.2

12/15/2008 9:36:59 AM TRAVERSE1 - 1 11.99 8.92 5.16 5.402083333

12/15/2008 9:37:29 AM Run Paused 11.92 8.92 5.6

12/15/2008 9:37:59 AM Run Paused 11.87 8.95 5.66

12/15/2008 9:38:29 AM Run Paused 13.45 8.02 4.61

12/15/2008 9:38:59 AM Run Paused 12.17 8.32 5.4

12/15/2008 9:39:29 AM Run Paused 11.94 8.91 5.56

12/15/2008 9:39:59 AM Run Paused 11.97 8.94 5.52

12/15/2008 9:40:29 AM TRAVERSE1 - 1 11.96 8.94 5.56

12/15/2008 9:40:59 AM TRAVERSE1 - 1 11.96 8.92 5.46

12/15/2008 9:41:29 AM TRAVERSE1 - 1 11.96 8.91 5.42

12/15/2008 9:41:59 AM TRAVERSE1 - 1 11.99 8.92 5.45

12/15/2008 9:42:29 AM TRAVERSE1 - 1 11.98 8.92 5.25

12/15/2008 9:42:59 AM TRAVERSE1 - 1 11.99 8.92 5.3

12/15/2008 9:43:29 AM TRAVERSE1 - 1 12.13 8.91 5.28

12/15/2008 9:43:59 AM TRAVERSE1 - 1 12.26 8.93 5.34

12/15/2008 9:44:29 AM TRAVERSE1 - 1 12.37 8.92 5.45

12/15/2008 9:44:59 AM TRAVERSE1 - 1 12.37 8.92 5.39

12/15/2008 9:45:29 AM TRAVERSE1 - 1 12.28 8.92 5.53

12/15/2008 9:45:59 AM TRAVERSE1 - 1 12.15 8.93 5.55

12/15/2008 9:46:29 AM TRAVERSE1 - 1 12.06 8.93 5.49

12/15/2008 9:46:59 AM TRAVERSE1 - 1 12 8.92 5.2

12/15/2008 9:47:29 AM TRAVERSE1 - 1 12.26 8.9 5.04

12/15/2008 9:47:59 AM TRAVERSE1 - 1 12.13 8.9 5.27

12/15/2008 9:48:29 AM TRAVERSE1 - 1 12.33 8.92 5.56

12/15/2008 9:48:59 AM TRAVERSE1 - 1 11.97 8.92 5.41

12/15/2008 9:49:29 AM TRAVERSE1 - 1 12.1 8.91 5.33

12/15/2008 9:49:59 AM TRAVERSE1 - 1 12.01 8.91 5.61

12/15/2008 9:50:29 AM TRAVERSE1 - 1 12.16 8.92 5.47

12/15/2008 9:50:59 AM TRAVERSE1 - 1 12.03 8.91 5.49

12/15/2008 9:51:29 AM TRAVERSE1 - 1 12.11 8.91 5.52

12/15/2008 9:51:59 AM TRAVERSE1 - 1 12.01 8.91 5.34 5.404583333

12/15/2008 9:52:29 AM Run Paused 11.99 8.9 5.37

12/15/2008 9:52:59 AM Run Paused 11.99 8.9 5.5

12/15/2008 9:53:29 AM Run Paused 11.95 8.89 5.78

12/15/2008 9:53:59 AM Run Paused 12.02 8.9 5.68

12/15/2008 9:54:29 AM Run Paused 12.09 8.89 5.71

12/15/2008 9:54:59 AM Run Paused 12.01 8.91 5.56

12/15/2008 9:55:29 AM Run Paused 12.73 8.7 4.26

12/15/2008 9:55:59 AM Run Paused 12.5 7.86 5.25

12/15/2008 9:56:29 AM Run Paused 12.21 8.87 5.45

12/15/2008 9:56:59 AM TRAVERSE1 - 1 12.01 8.88 5.49

12/15/2008 9:57:29 AM TRAVERSE1 - 1 12.15 8.89 5.48

12/15/2008 9:57:59 AM TRAVERSE1 - 1 12.02 8.89 5.92

12/15/2008 9:58:29 AM TRAVERSE1 - 1 11.97 8.92 5.79

12/15/2008 9:58:59 AM TRAVERSE1 - 1 11.93 8.89 5.78

12/15/2008 9:59:29 AM TRAVERSE1 - 1 12.11 8.93 5.63

Page 4 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 9:59:59 AM TRAVERSE1 - 1 11.98 8.89 5.52

12/15/2008 10:00:29 AM TRAVERSE1 - 1 12.12 8.88 5.53

12/15/2008 10:00:59 AM TRAVERSE1 - 1 12.38 8.9 5.45

12/15/2008 10:01:29 AM TRAVERSE1 - 1 12.38 8.88 5.45

12/15/2008 10:01:59 AM TRAVERSE1 - 1 12.23 8.9 5.23

12/15/2008 10:02:29 AM TRAVERSE1 - 1 12.12 8.88 5.26

12/15/2008 10:02:59 AM TRAVERSE1 - 1 12.12 8.88 5.39

12/15/2008 10:03:29 AM TRAVERSE1 - 1 12.05 8.89 5.4

12/15/2008 10:03:59 AM TRAVERSE1 - 1 12.04 8.89 5.42

12/15/2008 10:04:29 AM TRAVERSE1 - 1 12.05 8.89 5.33

12/15/2008 10:04:59 AM TRAVERSE1 - 1 12.04 8.88 5.38

12/15/2008 10:05:29 AM TRAVERSE1 - 1 12.15 8.89 5.22

12/15/2008 10:05:59 AM TRAVERSE1 - 1 12.15 8.9 4.99

12/15/2008 10:06:29 AM TRAVERSE1 - 1 12.17 8.92 4.6

12/15/2008 10:06:59 AM TRAVERSE1 - 1 12.17 8.92 5.16

12/15/2008 10:07:29 AM TRAVERSE1 - 1 12.16 8.88 5.33

12/15/2008 10:07:59 AM TRAVERSE1 - 1 12.14 8.9 5.42

12/15/2008 10:08:29 AM TRAVERSE1 - 1 12.11 8.9 5.16 5.38875

12/15/2008 10:08:59 AM Run Paused 12.14 8.88 5.03

12/15/2008 10:09:29 AM Run Paused 12.14 8.87 5.14

12/15/2008 10:09:59 AM Run Paused 12.16 8.89 4.97

12/15/2008 10:10:29 AM Run Paused 16.18 5.42 0.62

12/15/2008 10:10:59 AM Run Paused 18.37 2.1 4.21

12/15/2008 10:11:29 AM Run Paused 12.25 8.35 5.21

12/15/2008 10:11:59 AM Run Paused 12.22 8.85 5.27

12/15/2008 10:12:29 AM TRAVERSE1 - 1 12.06 8.88 5.18

12/15/2008 10:12:59 AM TRAVERSE1 - 1 12.32 8.88 4.95

12/15/2008 10:13:29 AM TRAVERSE1 - 1 12.41 8.88 4.98

12/15/2008 10:13:59 AM TRAVERSE1 - 1 12.4 8.87 4.96

12/15/2008 10:14:29 AM TRAVERSE1 - 1 12.41 8.86 5.28

12/15/2008 10:14:59 AM TRAVERSE1 - 1 12.38 8.88 5.36

12/15/2008 10:15:29 AM TRAVERSE1 - 1 12.16 8.89 5.16

12/15/2008 10:15:59 AM TRAVERSE1 - 1 12.14 8.87 5.14

12/15/2008 10:16:29 AM TRAVERSE1 - 1 12.19 8.88 5.25

12/15/2008 10:16:59 AM TRAVERSE1 - 1 12.34 8.89 4.98

12/15/2008 10:17:29 AM TRAVERSE1 - 1 12.16 8.87 5.04

12/15/2008 10:17:59 AM TRAVERSE1 - 1 12.41 8.87 5.05

12/15/2008 10:18:29 AM TRAVERSE1 - 1 12.41 8.87 5.23

12/15/2008 10:18:59 AM TRAVERSE1 - 1 12.39 8.87 5.41

12/15/2008 10:19:29 AM TRAVERSE1 - 1 12.39 8.88 5.32

12/15/2008 10:19:59 AM TRAVERSE1 - 1 12.39 8.88 5.21

12/15/2008 10:20:29 AM TRAVERSE1 - 1 12.39 8.89 5.14

12/15/2008 10:20:59 AM TRAVERSE1 - 1 12.39 8.86 4.96

12/15/2008 10:21:29 AM TRAVERSE1 - 1 12.41 8.88 4.78

12/15/2008 10:21:59 AM TRAVERSE1 - 1 12.41 8.86 4.96

12/15/2008 10:22:29 AM TRAVERSE1 - 1 12.36 8.86 5.19

12/15/2008 10:22:59 AM TRAVERSE1 - 1 12.36 8.88 5.12

12/15/2008 10:23:29 AM TRAVERSE1 - 1 12.38 8.87 5.03

12/15/2008 10:23:59 AM TRAVERSE1 - 1 12.37 8.86 4.99 5.11125

12/15/2008 10:24:29 AM 12.36 8.86 5.01

12/15/2008 10:24:59 AM 12.36 8.85 5.13

12/15/2008 10:25:29 AM 6.6 4.89 7.54

12/15/2008 10:25:59 AM 0.43 0.34 4.35

12/15/2008 10:26:29 AM - Span 0.25 0.07 4.36

Page 5 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 10:26:59 AM - Span 0.28 0.04 4.34

12/15/2008 10:27:29 AM - Span 0.18 0.03 3.97

12/15/2008 10:27:59 AM - Span 0.03 0.03 4

12/15/2008 10:28:29 AM - ZERO 0.03 0.02 3.96

12/15/2008 10:28:59 AM - ZERO 3.21 2.1 1.32

12/15/2008 10:29:29 AM - Span 10.19 7.91 0.2

12/15/2008 10:29:59 AM - Span 10.61 8.83 0.17

12/15/2008 10:30:29 AM - Span 10.52 8.87 0.16

12/15/2008 10:30:59 AM - Span 10.69 8.88 0.17

12/15/2008 10:31:29 AM - ZERO 10.69 8.89 0.16

12/15/2008 10:31:59 AM - ZERO 10.53 8.9 0.16

12/15/2008 10:32:29 AM - ZERO 10.54 8.9 0.22

12/15/2008 10:32:59 AM - ZERO 18.64 2.88 0.41

12/15/2008 10:33:29 AM - ZERO 20.87 0.17 0.47

12/15/2008 10:33:59 AM - ZERO 20.9 0.07 0.47

12/15/2008 10:34:29 AM - ZERO 20.91 0.05 -0.01

12/15/2008 10:34:59 AM - ZERO 20.92 0.03 0.01

12/15/2008 10:35:29 AM - ZERO 20.93 0.03 0

12/15/2008 10:35:59 AM - ZERO 20.88 0.02 1.47

12/15/2008 10:36:29 AM - ZERO 0.71 0.02 3.46

12/15/2008 10:36:59 AM - ZERO 0.11 0.01 3.45

12/15/2008 10:37:29 AM - ZERO 0.07 0.01 3.95

12/15/2008 10:37:59 AM - ZERO 0.05 0.01 4.01

12/15/2008 10:38:29 AM - ZERO 0.04 0.01 3.97

12/15/2008 10:38:59 AM - ZERO 4.94 3.02 4.53

12/15/2008 10:39:29 AM - ZERO 11.74 8.18 4.77

12/15/2008 10:39:59 AM - ZERO 12.26 8.81 4.51

12/15/2008 10:40:29 AM - ZERO 12.13 8.84 4.61

12/15/2008 10:40:59 AM - ZERO 12.08 8.85 4.65

12/15/2008 10:41:29 AM - ZERO 9.18 7.45 3.68

12/15/2008 10:41:59 AM - ZERO 0.16 0.58 3.18

12/15/2008 10:42:29 AM - ZERO 0 0.01 3.2

12/15/2008 10:42:59 AM - ZERO 0 0 3.99

12/15/2008 10:43:29 AM - ZERO 8.58 4.85 5.32

12/15/2008 10:43:59 AM - ZERO 4.49 3.83 5.15

12/15/2008 10:44:29 AM - ZERO 0.42 0.16 4.95

12/15/2008 10:44:59 AM - ZERO 0.34 0.04 4.97

12/15/2008 10:45:29 AM - ZERO 0.03 0.03 4.97

12/15/2008 10:45:59 AM - ZERO 0.03 0.02 4.96

12/15/2008 10:46:29 AM - ZERO 2.77 1.45 5.23

12/15/2008 10:46:59 AM - ZERO 11.49 7.73 5.71

12/15/2008 10:47:29 AM - ZERO 11.95 8.79 5.73

12/15/2008 10:47:59 AM - ZERO 8.95 7.38 5.54

12/15/2008 10:48:29 AM - ZERO 0.34 0.76 5

12/15/2008 10:48:59 AM - ZERO 0.05 0.05 4.99

12/15/2008 10:49:29 AM - ZERO 0.03 0.03 4.99

12/15/2008 10:49:59 AM - ZERO 0.02 0.02 3.98

12/15/2008 10:50:29 AM - ZERO 0.03 0.01 3.96

12/15/2008 10:50:59 AM - ZERO 7.09 4.5 4.47

12/15/2008 10:51:29 AM - ZERO 11.89 8.49 4.4

12/15/2008 10:51:59 AM - ZERO 11.99 8.78 4.38

12/15/2008 10:52:29 AM - ZERO 11.99 8.79 4.5

12/15/2008 10:52:59 AM - ZERO 11.96 8.81 4.7

12/15/2008 10:53:29 AM - ZERO 11.95 8.82 4.66

Page 6 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 10:53:59 AM - ZERO 11.97 8.81 4.61

12/15/2008 10:54:29 AM - ZERO 11.98 8.82 4.96

12/15/2008 10:54:59 AM - ZERO 11.98 8.82 4.95

12/15/2008 10:55:29 AM - ZERO 11.99 8.81 5.17

12/15/2008 10:55:59 AM - ZERO 12.02 8.81 5.06

12/15/2008 10:56:29 AM RUN 1 - 1 12.02 8.82 5.12

12/15/2008 10:56:59 AM RUN 1 - 1 12.02 8.81 5.16

12/15/2008 10:57:29 AM RUN 1 - 1 11.99 8.82 5.33

12/15/2008 10:57:59 AM RUN 1 - 1 12.2 8.83 5.32

12/15/2008 10:58:29 AM RUN 1 - 1 11.97 8.82 5.43

12/15/2008 10:58:59 AM RUN 1 - 1 12.13 8.83 5.4

12/15/2008 10:59:29 AM RUN 1 - 1 12.43 8.83 5.25

12/15/2008 10:59:59 AM RUN 1 - 1 12 8.82 5.21

12/15/2008 11:00:29 AM RUN 1 - 1 12 8.82 5.32

12/15/2008 11:00:59 AM RUN 1 - 1 12 8.84 5.27

12/15/2008 11:01:29 AM RUN 1 - 1 12 8.83 5.1

12/15/2008 11:01:59 AM RUN 1 - 1 12.02 8.81 5.14

12/15/2008 11:02:29 AM RUN 1 - 1 12.02 8.81 5.15

12/15/2008 11:02:59 AM RUN 1 - 1 12.02 8.82 5.08

12/15/2008 11:03:29 AM RUN 1 - 1 12.05 8.81 5.09

12/15/2008 11:03:59 AM RUN 1 - 1 12.01 8.82 5.26

12/15/2008 11:04:29 AM RUN 1 - 1 12.01 8.82 5.29

12/15/2008 11:04:59 AM RUN 1 - 1 11.99 8.81 5.44

12/15/2008 11:05:29 AM RUN 1 - 1 12 8.81 5.34

12/15/2008 11:05:59 AM RUN 1 - 1 12 8.81 5.33

12/15/2008 11:06:29 AM RUN 1 - 1 12.02 8.81 5

12/15/2008 11:06:59 AM RUN 1 - 1 12.02 8.83 4.43

12/15/2008 11:07:29 AM RUN 1 - 1 12.02 8.83 5.23

12/15/2008 11:07:59 AM RUN 1 - 1 12.01 8.82 5.35

12/15/2008 11:08:29 AM RUN 1 - 1 11.97 8.81 5.49

12/15/2008 11:08:59 AM RUN 1 - 1 11.96 8.82 5.49

12/15/2008 11:09:29 AM RUN 1 - 1 11.98 8.81 5.42

12/15/2008 11:09:59 AM RUN 1 - 1 11.98 8.81 5.37

12/15/2008 11:10:29 AM RUN 1 - 1 11.99 8.81 5.12

12/15/2008 11:10:59 AM RUN 1 - 1 12 8.8 5.29

12/15/2008 11:11:29 AM RUN 1 - 1 11.96 8.83 5.36

12/15/2008 11:11:59 AM RUN 1 - 1 11.96 8.81 5.49

12/15/2008 11:12:29 AM RUN 1 - 1 11.94 8.8 5.69

12/15/2008 11:12:59 AM RUN 1 - 1 11.94 8.82 5.52

12/15/2008 11:13:29 AM RUN 1 - 1 11.95 8.81 5.49

12/15/2008 11:13:59 AM RUN 1 - 1 11.96 8.81 5.17

12/15/2008 11:14:29 AM RUN 1 - 1 12.07 8.8 5.25

12/15/2008 11:14:59 AM RUN 1 - 1 12.06 8.81 5.33

12/15/2008 11:15:29 AM RUN 1 - 1 11.91 8.82 5.49

12/15/2008 11:15:59 AM RUN 1 - 1 12.06 8.82 5.48

12/15/2008 11:16:29 AM RUN 1 - 1 12.06 8.82 5.5

12/15/2008 11:16:59 AM RUN 1 - 1 12.01 8.83 5.51

12/15/2008 11:17:29 AM RUN 1 - 1 12.23 8.81 5.31

12/15/2008 11:17:59 AM RUN 1 - 1 12.16 8.8 5.69

12/15/2008 11:18:29 AM RUN 1 - 1 12.1 8.81 5.59

12/15/2008 11:18:59 AM RUN 1 - 1 12.35 8.81 5.66

12/15/2008 11:19:29 AM RUN 1 - 1 12.19 8.82 5.47

12/15/2008 11:19:59 AM RUN 1 - 1 12.13 8.81 5.51

12/15/2008 11:20:29 AM RUN 1 - 1 12.35 8.82 5.48

Page 7 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 11:20:59 AM RUN 1 - 1 12.12 8.82 5.24

12/15/2008 11:21:29 AM RUN 1 - 1 12.11 8.8 5.14

12/15/2008 11:21:59 AM RUN 1 - 1 12.18 8.8 5.17

12/15/2008 11:22:29 AM RUN 1 - 1 12.17 8.8 5.04

12/15/2008 11:22:59 AM RUN 1 - 1 12.19 8.79 5.11

12/15/2008 11:23:29 AM RUN 1 - 1 12.21 8.79 5.2

12/15/2008 11:23:59 AM RUN 1 - 1 12.12 8.8 5.21

12/15/2008 11:24:29 AM RUN 1 - 1 12.17 8.78 5.25

12/15/2008 11:24:59 AM RUN 1 - 1 12.23 8.81 5.19

12/15/2008 11:25:29 AM RUN 1 - 1 12.22 8.81 5.15

12/15/2008 11:25:59 AM RUN 1 - 1 12.24 8.78 5.27

12/15/2008 11:26:29 AM RUN 1 - 1 12.26 8.79 5.28

12/15/2008 11:26:59 AM RUN 1 - 1 12.24 8.8 5.07

12/15/2008 11:27:29 AM RUN 1 - 1 12.27 8.78 5.18

12/15/2008 11:27:59 AM RUN 1 - 1 12.11 8.78 5.3

12/15/2008 11:28:29 AM RUN 1 - 1 12.12 8.78 5.46

12/15/2008 11:28:59 AM RUN 1 - 1 12.17 8.79 5.36

12/15/2008 11:29:29 AM RUN 1 - 1 12.11 8.8 5.34

12/15/2008 11:29:59 AM RUN 1 - 1 12.13 8.79 5.15

12/15/2008 11:30:29 AM RUN 1 - 1 12.12 8.8 5.22

12/15/2008 11:30:59 AM RUN 1 - 1 12.17 8.8 5.25

12/15/2008 11:31:29 AM RUN 1 - 1 12.16 8.81 5.22

12/15/2008 11:31:59 AM RUN 1 - 1 12.16 8.8 5.39

12/15/2008 11:32:29 AM RUN 1 - 1 12.2 8.82 5.37

12/15/2008 11:32:59 AM RUN 1 - 1 12.19 8.81 5.3

12/15/2008 11:33:29 AM RUN 1 - 1 12.18 8.79 5.45

12/15/2008 11:33:59 AM RUN 1 - 1 12.19 8.8 5.43

12/15/2008 11:34:29 AM RUN 1 - 1 12.16 8.79 5.39

12/15/2008 11:34:59 AM RUN 1 - 1 12.16 8.81 5.41

12/15/2008 11:35:29 AM RUN 1 - 1 12.22 8.81 5.45

12/15/2008 11:35:59 AM RUN 1 - 1 12.22 8.83 5.27

12/15/2008 11:36:29 AM RUN 1 - 1 12.22 8.81 5.39

12/15/2008 11:36:59 AM RUN 1 - 1 12.19 8.81 5.18

12/15/2008 11:37:29 AM RUN 1 - 1 12.2 8.8 5.41

12/15/2008 11:37:59 AM RUN 1 - 1 12.15 8.79 5.5

12/15/2008 11:38:29 AM RUN 1 - 1 12.17 8.8 5.45

12/15/2008 11:38:59 AM RUN 1 - 1 12.19 8.8 5.51

12/15/2008 11:39:29 AM RUN 1 - 1 12.13 8.8 5.54

12/15/2008 11:39:59 AM RUN 1 - 1 12.23 8.8 5.5

12/15/2008 11:40:29 AM RUN 1 - 1 12.29 8.8 5.21

12/15/2008 11:40:59 AM RUN 1 - 1 12.19 8.79 5.12

12/15/2008 11:41:29 AM RUN 1 - 1 12.16 8.79 5.3

12/15/2008 11:41:59 AM RUN 1 - 1 12.15 8.8 5.46

12/15/2008 11:42:29 AM RUN 1 - 1 12.13 8.81 5.45

12/15/2008 11:42:59 AM RUN 1 - 1 12.15 8.82 5.47

12/15/2008 11:43:29 AM RUN 1 - 1 12.15 8.8 5.48

12/15/2008 11:43:59 AM RUN 1 - 1 12.16 8.82 5.26

12/15/2008 11:44:29 AM RUN 1 - 1 12.19 8.8 5.19

12/15/2008 11:44:59 AM RUN 1 - 1 12.17 8.8 5.3

12/15/2008 11:45:29 AM RUN 1 - 1 12.16 8.81 5.47

12/15/2008 11:45:59 AM RUN 1 - 1 12.13 8.82 5.37

12/15/2008 11:46:29 AM RUN 1 - 1 12.16 8.8 5.55

12/15/2008 11:46:59 AM RUN 1 - 1 12.18 8.83 5.52

12/15/2008 11:47:29 AM RUN 1 - 1 12.16 8.81 5.62

Page 8 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 11:47:59 AM RUN 1 - 1 12.17 8.82 5.45

12/15/2008 11:48:29 AM RUN 1 - 1 12.2 8.81 5.32

12/15/2008 11:48:59 AM RUN 1 - 1 12.23 8.8 5.36

12/15/2008 11:49:29 AM RUN 1 - 1 12.22 8.8 5.33

12/15/2008 11:49:59 AM RUN 1 - 1 12.22 8.8 5.27

12/15/2008 11:50:29 AM RUN 1 - 1 12.21 8.81 5.32

12/15/2008 11:50:59 AM RUN 1 - 1 12.23 8.8 5.49

12/15/2008 11:51:29 AM RUN 1 - 1 12.22 8.81 5.46

12/15/2008 11:51:59 AM RUN 1 - 1 12.23 8.8 5.37

12/15/2008 11:52:29 AM RUN 1 - 1 12.25 8.81 5.33

12/15/2008 11:52:59 AM RUN 1 - 1 12.24 8.81 5.29

12/15/2008 11:53:29 AM RUN 1 - 1 12.26 8.8 5.18

12/15/2008 11:53:59 AM RUN 1 - 1 12.25 8.81 5.32

12/15/2008 11:54:29 AM RUN 1 - 1 12.23 8.8 5.53

12/15/2008 11:54:59 AM RUN 1 - 1 12.21 8.81 5.37

12/15/2008 11:55:29 AM RUN 1 - 1 12.22 8.79 5.32

12/15/2008 11:55:59 AM RUN 1 - 1 12.22 8.79 5.31

12/15/2008 11:56:29 AM 12.21 8.79 5.31

12/15/2008 11:56:59 AM 12.23 8.8 8.05

12/15/2008 11:57:29 AM 4.55 3.24 9.55

12/15/2008 11:57:59 AM 0.46 0.17 4.87

12/15/2008 11:58:29 AM 0.35 0.06 4.89

12/15/2008 11:58:59 AM 0.23 0.04 4.86

12/15/2008 11:59:29 AM 0.24 0.03 4.86

12/15/2008 11:59:59 AM - ZERO 0.25 0.02 4.86

12/15/2008 12:00:29 PM - ZERO 0.21 0.02 3.82

12/15/2008 12:00:59 PM - Span 0.21 0.02 3.96

12/15/2008 12:01:29 PM - Span 0.21 0.02 3.98

12/15/2008 12:01:59 PM - ZERO 0.16 0.01 3.88

12/15/2008 12:02:29 PM - ZERO 5.98 4.29 0.59

12/15/2008 12:02:59 PM - ZERO 10.51 8.49 0.02

12/15/2008 12:03:29 PM - Span 10.59 8.82 -0.02

12/15/2008 12:03:59 PM - ZERO 10.6 8.84 -0.01

12/15/2008 12:04:29 PM - ZERO 10.52 8.86 -0.01

12/15/2008 12:04:59 PM - ZERO 10.51 8.87 1.03

12/15/2008 12:05:29 PM - ZERO 11.8 8.83 4.28

12/15/2008 12:05:59 PM - ZERO 11.99 8.83 4.32

12/15/2008 12:06:29 PM - ZERO 12.02 8.81 4.29

12/15/2008 12:06:59 PM - ZERO 12 8.8 5.06

12/15/2008 12:07:29 PM - ZERO 11.95 8.82 4.83

12/15/2008 12:07:59 PM - ZERO 11.9 8.85 5.69

12/15/2008 12:08:29 PM - ZERO 11.93 8.82 5.69

12/15/2008 12:08:59 PM - ZERO 11.92 8.81 5.55

12/15/2008 12:09:29 PM - ZERO 11.97 8.8 5.14

12/15/2008 12:09:59 PM - ZERO 11.98 8.79 4.66

12/15/2008 12:10:29 PM - ZERO 3.21 3.48 4.66

12/15/2008 12:10:59 PM - ZERO 0.08 0.17 4.78

12/15/2008 12:11:29 PM - ZERO 0.05 0.07 4.8

12/15/2008 12:11:59 PM - ZERO 0.04 0.05 3.99

12/15/2008 12:12:29 PM - ZERO 0.03 0.04 4

12/15/2008 12:12:59 PM - ZERO 4.36 2.7 4.22

12/15/2008 12:13:29 PM - ZERO 11.63 7.96 4.54

12/15/2008 12:13:59 PM - ZERO 11.94 8.75 4.96

12/15/2008 12:14:29 PM - ZERO 11.96 8.77 5.03

Page 9 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 12:14:59 PM - ZERO 11.96 8.79 5.01

12/15/2008 12:15:29 PM - ZERO 11.99 8.78 4.99

12/15/2008 12:15:59 PM - ZERO 12 8.78 4.89

12/15/2008 12:16:29 PM - ZERO 11.99 8.79 4.9

12/15/2008 12:16:59 PM RUN 2 - 1 11.96 8.8 5.14

12/15/2008 12:17:29 PM RUN 2 - 1 11.97 8.8 5.08

12/15/2008 12:17:59 PM RUN 2 - 1 11.96 8.78 5.08

12/15/2008 12:18:29 PM RUN 2 - 1 11.96 8.8 5.09

12/15/2008 12:18:59 PM RUN 2 - 1 11.95 8.79 5.22

12/15/2008 12:19:29 PM RUN 2 - 1 11.95 8.8 5.27

12/15/2008 12:19:59 PM RUN 2 - 1 12.01 8.79 5.25

12/15/2008 12:20:29 PM RUN 2 - 1 11.98 8.8 5.1

12/15/2008 12:20:59 PM RUN 2 - 1 12.04 8.78 5.05

12/15/2008 12:21:29 PM RUN 2 - 1 12.06 8.8 5.01

12/15/2008 12:21:59 PM RUN 2 - 1 12.04 8.81 4.82

12/15/2008 12:22:29 PM RUN 2 - 1 12.01 8.8 5.08

12/15/2008 12:22:59 PM RUN 2 - 1 11.97 8.8 5.26

12/15/2008 12:23:29 PM RUN 2 - 1 12.04 8.79 5.27

12/15/2008 12:23:59 PM RUN 2 - 1 11.99 8.81 5.15

12/15/2008 12:24:29 PM RUN 2 - 1 11.98 8.79 5.19

12/15/2008 12:24:59 PM RUN 2 - 1 12.01 8.79 5.16

12/15/2008 12:25:29 PM RUN 2 - 1 12 8.8 5.11

12/15/2008 12:25:59 PM RUN 2 - 1 12.03 8.79 5.01

12/15/2008 12:26:29 PM RUN 2 - 1 12.02 8.79 5.15

12/15/2008 12:26:59 PM RUN 2 - 1 11.99 8.79 5.33

12/15/2008 12:27:29 PM RUN 2 - 1 11.95 8.81 5.23

12/15/2008 12:27:59 PM RUN 2 - 1 11.99 8.78 5.31

12/15/2008 12:28:29 PM RUN 2 - 1 11.94 8.79 5.34

12/15/2008 12:28:59 PM RUN 2 - 1 11.96 8.78 5.32

12/15/2008 12:29:29 PM RUN 2 - 1 11.96 8.78 5.19

12/15/2008 12:29:59 PM RUN 2 - 1 11.98 8.77 5.15

12/15/2008 12:30:29 PM RUN 2 - 1 11.97 8.79 5.36

12/15/2008 12:30:59 PM RUN 2 - 1 11.97 8.79 5.39

12/15/2008 12:31:29 PM RUN 2 - 1 11.91 8.79 5.53

12/15/2008 12:31:59 PM RUN 2 - 1 11.92 8.8 5.59

12/15/2008 12:32:29 PM RUN 2 - 1 11.91 8.81 5.56

12/15/2008 12:32:59 PM RUN 2 - 1 11.94 8.79 5.51

12/15/2008 12:33:29 PM RUN 2 - 1 11.94 8.8 5.47

12/15/2008 12:33:59 PM RUN 2 - 1 11.96 8.8 5.29

12/15/2008 12:34:29 PM RUN 2 - 1 11.98 8.79 5.26

12/15/2008 12:34:59 PM RUN 2 - 1 11.96 8.8 5.41

12/15/2008 12:35:29 PM RUN 2 - 1 11.97 8.8 5.26

12/15/2008 12:35:59 PM RUN 2 - 1 11.95 8.78 5.42

12/15/2008 12:36:29 PM RUN 2 - 1 11.92 8.8 5.33

12/15/2008 12:36:59 PM RUN 2 - 1 11.97 8.78 5.39

12/15/2008 12:37:29 PM RUN 2 - 1 11.96 8.79 5.45

12/15/2008 12:37:59 PM RUN 2 - 1 11.9 8.79 5.64

12/15/2008 12:38:29 PM RUN 2 - 1 11.9 8.8 5.52

12/15/2008 12:38:59 PM RUN 2 - 1 11.95 8.78 5.43

12/15/2008 12:39:29 PM RUN 2 - 1 11.94 8.81 5.41

12/15/2008 12:39:59 PM RUN 2 - 1 11.96 8.79 5.29

12/15/2008 12:40:29 PM RUN 2 - 1 11.97 8.79 5.23

12/15/2008 12:40:59 PM RUN 2 - 1 11.99 8.78 5.25

12/15/2008 12:41:29 PM RUN 2 - 1 12 8.79 5.3

Page 10 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 12:41:59 PM RUN 2 - 1 11.97 8.8 5.38

12/15/2008 12:42:29 PM RUN 2 - 1 12 8.8 5.22

12/15/2008 12:42:59 PM RUN 2 - 1 11.99 8.78 5.25

12/15/2008 12:43:29 PM RUN 2 - 1 11.97 8.79 5.34

12/15/2008 12:43:59 PM RUN 2 - 1 11.99 8.8 5.18

12/15/2008 12:44:29 PM RUN 2 - 1 12.02 8.79 5

12/15/2008 12:44:59 PM RUN 2 - 1 11.98 8.79 5.28

12/15/2008 12:45:29 PM RUN 2 - 1 11.98 8.78 5.1

12/15/2008 12:45:59 PM RUN 2 - 1 11.98 8.78 5.06

12/15/2008 12:46:29 PM RUN 2 - 1 11.99 8.77 5.14

12/15/2008 12:46:59 PM RUN 2 - 1 11.98 8.78 5.23

12/15/2008 12:47:29 PM RUN 2 - 1 11.98 8.78 5.25

12/15/2008 12:47:59 PM RUN 2 - 1 11.98 8.8 5.19

12/15/2008 12:48:29 PM RUN 2 - 1 11.98 8.8 5.09

12/15/2008 12:48:59 PM RUN 2 - 1 11.97 8.8 4.97

12/15/2008 12:49:29 PM RUN 2 - 1 11.96 8.79 5.17

12/15/2008 12:49:59 PM RUN 2 - 1 11.95 8.79 5.3

12/15/2008 12:50:29 PM RUN 2 - 1 11.95 8.79 5.31

12/15/2008 12:50:59 PM RUN 2 - 1 11.95 8.81 5.23

12/15/2008 12:51:29 PM RUN 2 - 1 11.96 8.79 5.23

12/15/2008 12:51:59 PM RUN 2 - 1 11.95 8.79 5.25

12/15/2008 12:52:29 PM RUN 2 - 1 11.95 8.79 5.19

12/15/2008 12:52:59 PM RUN 2 - 1 11.96 8.78 5.3

12/15/2008 12:53:29 PM RUN 2 - 1 11.98 8.79 5.25

12/15/2008 12:53:59 PM RUN 2 - 1 11.97 8.79 5.17

12/15/2008 12:54:29 PM RUN 2 - 1 12 8.79 4.91

12/15/2008 12:54:59 PM RUN 2 - 1 11.99 8.78 5.03

12/15/2008 12:55:29 PM RUN 2 - 1 11.98 8.78 5.25

12/15/2008 12:55:59 PM RUN 2 - 1 11.94 8.78 5.38

12/15/2008 12:56:29 PM RUN 2 - 1 11.94 8.8 5.27

12/15/2008 12:56:59 PM RUN 2 - 1 11.98 8.78 5.22

12/15/2008 12:57:29 PM RUN 2 - 1 11.96 8.79 5.3

12/15/2008 12:57:59 PM RUN 2 - 1 11.95 8.8 5.34

12/15/2008 12:58:29 PM RUN 2 - 1 11.95 8.8 5.2

12/15/2008 12:58:59 PM RUN 2 - 1 11.96 8.79 5.25

12/15/2008 12:59:29 PM RUN 2 - 1 11.95 8.79 5.34

12/15/2008 12:59:59 PM RUN 2 - 1 11.95 8.8 5.29

12/15/2008 1:00:29 PM RUN 2 - 1 11.95 8.8 5.34

12/15/2008 1:00:59 PM RUN 2 - 1 11.94 8.82 5.27

12/15/2008 1:01:29 PM RUN 2 - 1 11.97 8.81 5.19

12/15/2008 1:01:59 PM RUN 2 - 1 11.98 8.8 5.05

12/15/2008 1:02:29 PM RUN 2 - 1 12 8.79 4.95

12/15/2008 1:02:59 PM RUN 2 - 1 12.02 8.78 5.01

12/15/2008 1:03:29 PM RUN 2 - 1 11.99 8.79 5.09

12/15/2008 1:03:59 PM RUN 2 - 1 12 8.79 5.28

12/15/2008 1:04:29 PM RUN 2 - 1 11.97 8.82 5.24

12/15/2008 1:04:59 PM RUN 2 - 1 11.99 8.79 5.06

12/15/2008 1:05:29 PM RUN 2 - 1 12 8.79 5.25

12/15/2008 1:05:59 PM RUN 2 - 1 12.01 8.79 5.02

12/15/2008 1:06:29 PM RUN 2 - 1 12.02 8.78 4.85

12/15/2008 1:06:59 PM RUN 2 - 1 12.05 8.78 4.95

12/15/2008 1:07:29 PM RUN 2 - 1 12.05 8.79 4.97

12/15/2008 1:07:59 PM RUN 2 - 1 11.98 8.82 4.58

12/15/2008 1:08:29 PM RUN 2 - 1 11.96 8.81 5.27

Page 11 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 1:08:59 PM RUN 2 - 1 11.98 8.79 5.28

12/15/2008 1:09:29 PM RUN 2 - 1 11.99 8.8 5.27

12/15/2008 1:09:59 PM RUN 2 - 1 12 8.81 5.05

12/15/2008 1:10:29 PM RUN 2 - 1 12.03 8.8 5.01

12/15/2008 1:10:59 PM RUN 2 - 1 12.02 8.78 5.05

12/15/2008 1:11:29 PM RUN 2 - 1 12.01 8.8 5.11

12/15/2008 1:11:59 PM RUN 2 - 1 12.02 8.81 5.08

12/15/2008 1:12:29 PM RUN 2 - 1 12.01 8.79 5.26

12/15/2008 1:12:59 PM RUN 2 - 1 12 8.81 5.37

12/15/2008 1:13:29 PM RUN 2 - 1 11.98 8.81 5.29

12/15/2008 1:13:59 PM RUN 2 - 1 11.98 8.8 5.28

12/15/2008 1:14:29 PM RUN 2 - 1 11.99 8.81 5.18

12/15/2008 1:14:59 PM RUN 2 - 1 12 8.8 5.08

12/15/2008 1:15:29 PM RUN 2 - 1 12.03 8.81 5.12

12/15/2008 1:15:59 PM RUN 2 - 1 12.02 8.81 5.12

12/15/2008 1:16:29 PM RUN 2 - 1 12.01 8.8 5.15

12/15/2008 1:16:59 PM 11.95 8.82 5.37

12/15/2008 1:17:29 PM 11.91 8.83 10

12/15/2008 1:17:59 PM 1.45 1.58 7.01

12/15/2008 1:18:29 PM 0.13 0.11 4.67

12/15/2008 1:18:59 PM - Span 0.12 0.05 3.97

12/15/2008 1:19:29 PM - Span 0.11 0.04 3.94

12/15/2008 1:19:59 PM - ZERO 0.1 0.03 3.97

12/15/2008 1:20:29 PM - ZERO 0.03 0.02 3.95

12/15/2008 1:20:59 PM - ZERO 0.03 0.02 3.76

12/15/2008 1:21:29 PM - ZERO 7.1 5.05 0.53

12/15/2008 1:21:59 PM - ZERO 10.44 8.57 0.06

12/15/2008 1:22:29 PM - ZERO 10.49 8.8 0.07

12/15/2008 1:22:59 PM - Span 10.5 8.83 0.06

12/15/2008 1:23:29 PM - Span 10.5 8.84 0.05

12/15/2008 1:23:59 PM - ZERO 10.5 8.84 0.07

12/15/2008 1:24:29 PM - ZERO 10.51 8.85 0.05

12/15/2008 1:24:59 PM - ZERO 10.51 8.86 0.04

12/15/2008 1:25:29 PM - ZERO 15.87 5.24 0.3

12/15/2008 1:25:59 PM - ZERO 20.66 0.26 1.99

12/15/2008 1:26:29 PM - ZERO 12.46 7.49 4.22

12/15/2008 1:26:59 PM - ZERO 12.02 8.74 4.21

12/15/2008 1:27:29 PM - ZERO 11.99 8.76 4.34

12/15/2008 1:27:59 PM - ZERO 11.95 8.77 4.58

12/15/2008 1:28:29 PM - ZERO 11.9 8.79 4.74

12/15/2008 1:28:59 PM - ZERO 11.9 8.8 5.07

12/15/2008 1:29:29 PM RUN 3 - 1 11.94 8.81 4.87

12/15/2008 1:29:59 PM RUN 3 - 1 11.95 8.8 4.81

12/15/2008 1:30:29 PM RUN 3 - 1 11.96 8.8 4.73

12/15/2008 1:30:59 PM RUN 3 - 1 11.98 8.79 4.68

12/15/2008 1:31:29 PM RUN 3 - 1 11.99 8.79 4.57

12/15/2008 1:31:59 PM RUN 3 - 1 12.01 8.78 4.54

12/15/2008 1:32:29 PM RUN 3 - 1 11.98 8.79 4.74

12/15/2008 1:32:59 PM RUN 3 - 1 11.97 8.79 4.94

12/15/2008 1:33:29 PM RUN 3 - 1 11.96 8.79 5.08

12/15/2008 1:33:59 PM RUN 3 - 1 11.99 8.79 4.92

12/15/2008 1:34:29 PM RUN 3 - 1 11.98 8.78 5.25

12/15/2008 1:34:59 PM RUN 3 - 1 11.99 8.78 5.21

12/15/2008 1:35:29 PM RUN 3 - 1 11.99 8.79 5.13

Page 12 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 1:35:59 PM RUN 3 - 1 12.01 8.79 5.15

12/15/2008 1:36:29 PM RUN 3 - 1 11.99 8.79 5.21

12/15/2008 1:36:59 PM RUN 3 - 1 12 8.78 5.15

12/15/2008 1:37:29 PM RUN 3 - 1 12 8.77 5.23

12/15/2008 1:37:59 PM RUN 3 - 1 11.96 8.78 5.26

12/15/2008 1:38:29 PM RUN 3 - 1 11.96 8.76 5.33

12/15/2008 1:38:59 PM RUN 3 - 1 11.97 8.77 5.28

12/15/2008 1:39:29 PM RUN 3 - 1 11.99 8.77 5.23

12/15/2008 1:39:59 PM RUN 3 - 1 12 8.77 5.14

12/15/2008 1:40:29 PM RUN 3 - 1 12 8.77 5.17

12/15/2008 1:40:59 PM RUN 3 - 1 11.98 8.77 5.29

12/15/2008 1:41:29 PM RUN 3 - 1 11.99 8.77 5.14

12/15/2008 1:41:59 PM RUN 3 - 1 12.01 8.78 5.11

12/15/2008 1:42:29 PM RUN 3 - 1 12 8.78 5.18

12/15/2008 1:42:59 PM RUN 3 - 1 11.98 8.76 5.32

12/15/2008 1:43:29 PM RUN 3 - 1 11.97 8.78 5.3

12/15/2008 1:43:59 PM RUN 3 - 1 11.98 8.76 5.29

12/15/2008 1:44:29 PM RUN 3 - 1 11.95 8.78 5.34

12/15/2008 1:44:59 PM RUN 3 - 1 11.97 8.76 5.43

12/15/2008 1:45:29 PM RUN 3 - 1 11.96 8.78 5.32

12/15/2008 1:45:59 PM RUN 3 - 1 11.95 8.77 5.36

12/15/2008 1:46:29 PM RUN 3 - 1 11.97 8.78 5.25

12/15/2008 1:46:59 PM RUN 3 - 1 11.99 8.76 5.34

12/15/2008 1:47:29 PM RUN 3 - 1 11.94 8.8 5.53

12/15/2008 1:47:59 PM RUN 3 - 1 11.91 8.77 5.77

12/15/2008 1:48:29 PM RUN 3 - 1 11.87 8.8 5.66

12/15/2008 1:48:59 PM RUN 3 - 1 11.9 8.77 5.25

12/15/2008 1:49:29 PM RUN 3 - 1 11.91 8.77 5.15

12/15/2008 1:49:59 PM RUN 3 - 1 11.9 8.78 5.13

12/15/2008 1:50:29 PM RUN 3 - 1 11.92 8.77 5.05

12/15/2008 1:50:59 PM RUN 3 - 1 11.96 8.78 4.87

12/15/2008 1:51:29 PM RUN 3 - 1 11.95 8.76 4.87

12/15/2008 1:51:59 PM RUN 3 - 1 11.94 8.75 5.05

12/15/2008 1:52:29 PM RUN 3 - 1 11.92 8.77 5.03

12/15/2008 1:52:59 PM RUN 3 - 1 11.93 8.77 5.1

12/15/2008 1:53:29 PM RUN 3 - 1 11.93 8.77 5.11

12/15/2008 1:53:59 PM RUN 3 - 1 11.92 8.79 4.94

12/15/2008 1:54:29 PM RUN 3 - 1 11.94 8.77 4.93

12/15/2008 1:54:59 PM RUN 3 - 1 11.9 8.77 5.1

12/15/2008 1:55:29 PM RUN 3 - 1 11.94 8.77 4.94

12/15/2008 1:55:59 PM RUN 3 - 1 11.94 8.77 4.9

12/15/2008 1:56:29 PM RUN 3 - 1 11.95 8.76 4.9

12/15/2008 1:56:59 PM RUN 3 - 1 11.97 8.76 4.84

12/15/2008 1:57:29 PM RUN 3 - 1 11.97 8.76 5.24

12/15/2008 1:57:59 PM RUN 3 - 1 11.9 8.77 5.42

12/15/2008 1:58:29 PM RUN 3 - 1 11.87 8.77 5.42

12/15/2008 1:58:59 PM RUN 3 - 1 11.9 8.76 5.31

12/15/2008 1:59:29 PM RUN 3 - 1 11.95 8.75 5.15

12/15/2008 1:59:59 PM RUN 3 - 1 11.95 8.76 5.15

12/15/2008 2:00:29 PM RUN 3 - 1 11.98 8.75 5.04

12/15/2008 2:00:59 PM RUN 3 - 1 11.98 8.76 4.94

12/15/2008 2:01:29 PM RUN 3 - 1 12 8.75 4.93

12/15/2008 2:01:59 PM RUN 3 - 1 11.98 8.76 5.02

12/15/2008 2:02:29 PM RUN 3 - 1 11.98 8.75 5.15

Page 13 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 2:02:59 PM RUN 3 - 1 11.95 8.76 5.18

12/15/2008 2:03:29 PM RUN 3 - 1 11.95 8.76 5.2

12/15/2008 2:03:59 PM RUN 3 - 1 11.96 8.77 5.05

12/15/2008 2:04:29 PM RUN 3 - 1 11.95 8.76 5.18

12/15/2008 2:04:59 PM RUN 3 - 1 11.96 8.75 5.07

12/15/2008 2:05:29 PM RUN 3 - 1 11.97 8.76 4.96

12/15/2008 2:05:59 PM RUN 3 - 1 12.01 8.75 4.82

12/15/2008 2:06:29 PM RUN 3 - 1 12 8.75 4.8

12/15/2008 2:06:59 PM RUN 3 - 1 11.99 8.76 4.99

12/15/2008 2:07:29 PM RUN 3 - 1 11.96 8.75 5.07

12/15/2008 2:07:59 PM RUN 3 - 1 11.96 8.75 5.06

12/15/2008 2:08:29 PM RUN 3 - 1 11.92 8.78 4.57

12/15/2008 2:08:59 PM RUN 3 - 1 11.94 8.78 5.09

12/15/2008 2:09:29 PM RUN 3 - 1 11.96 8.76 4.95

12/15/2008 2:09:59 PM RUN 3 - 1 11.98 8.73 5.03

12/15/2008 2:10:29 PM RUN 3 - 1 11.97 8.76 5.04

12/15/2008 2:10:59 PM RUN 3 - 1 11.97 8.75 5.02

12/15/2008 2:11:29 PM RUN 3 - 1 11.98 8.74 5.06

12/15/2008 2:11:59 PM RUN 3 - 1 11.99 8.76 5.02

12/15/2008 2:12:29 PM RUN 3 - 1 12.01 8.75 4.99

12/15/2008 2:12:59 PM RUN 3 - 1 12 8.74 4.92

12/15/2008 2:13:29 PM RUN 3 - 1 11.99 8.73 4.97

12/15/2008 2:13:59 PM RUN 3 - 1 11.98 8.75 4.97

12/15/2008 2:14:29 PM RUN 3 - 1 11.98 8.75 4.93

12/15/2008 2:14:59 PM RUN 3 - 1 11.98 8.75 5.04

12/15/2008 2:15:29 PM RUN 3 - 1 11.98 8.76 5.09

12/15/2008 2:15:59 PM RUN 3 - 1 11.98 8.75 5.03

12/15/2008 2:16:29 PM RUN 3 - 1 11.98 8.75 5.16

12/15/2008 2:16:59 PM RUN 3 - 1 11.95 8.76 5.18

12/15/2008 2:17:29 PM RUN 3 - 1 11.96 8.75 5.08

12/15/2008 2:17:59 PM RUN 3 - 1 11.98 8.75 5.17

12/15/2008 2:18:29 PM RUN 3 - 1 11.96 8.77 5.15

12/15/2008 2:18:59 PM RUN 3 - 1 11.98 8.75 5.02

12/15/2008 2:19:29 PM RUN 3 - 1 11.99 8.75 4.99

12/15/2008 2:19:59 PM RUN 3 - 1 11.98 8.76 5

12/15/2008 2:20:29 PM RUN 3 - 1 11.99 8.74 4.96

12/15/2008 2:20:59 PM RUN 3 - 1 12 8.75 4.9

12/15/2008 2:21:29 PM RUN 3 - 1 12.02 8.75 4.89

12/15/2008 2:21:59 PM RUN 3 - 1 12.03 8.75 4.92

12/15/2008 2:22:29 PM RUN 3 - 1 12.03 8.75 4.87

12/15/2008 2:22:59 PM RUN 3 - 1 11.99 8.75 5.1

12/15/2008 2:23:29 PM RUN 3 - 1 11.97 8.76 5.11

12/15/2008 2:23:59 PM RUN 3 - 1 11.99 8.76 5.09

12/15/2008 2:24:29 PM RUN 3 - 1 11.98 8.76 5.06

12/15/2008 2:24:59 PM RUN 3 - 1 12 8.76 5.06

12/15/2008 2:25:29 PM RUN 3 - 1 12 8.75 4.93

12/15/2008 2:25:59 PM RUN 3 - 1 12.01 8.74 5.06

12/15/2008 2:26:29 PM RUN 3 - 1 11.99 8.76 5.06

12/15/2008 2:26:59 PM RUN 3 - 1 11.99 8.76 4.99

12/15/2008 2:27:29 PM RUN 3 - 1 12.01 8.75 4.87

12/15/2008 2:27:59 PM RUN 3 - 1 11.99 8.74 5.09

12/15/2008 2:28:29 PM RUN 3 - 1 11.96 8.74 5.26

12/15/2008 2:28:59 PM RUN 3 - 1 11.96 8.76 5.22

12/15/2008 2:29:29 PM RUN 3 - 2 11.98 8.74 5.16

Page 14 of 15
LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 2:29:59 PM 11.98 8.74 5.11

12/15/2008 2:30:29 PM 12.02 8.73 10

12/15/2008 2:30:59 PM 9.09 5 3.73

12/15/2008 2:31:29 PM 10.51 8.61 0.39

12/15/2008 2:31:59 PM - Span 10.52 8.81 0.34

12/15/2008 2:32:29 PM - Span 10.52 8.83 0.33

12/15/2008 2:32:59 PM - Span 10.52 8.84 0.37

12/15/2008 2:33:29 PM - Span 10.51 8.83 0.3

12/15/2008 2:33:59 PM - Span 16.25 4.93 0.61

12/15/2008 2:34:29 PM - Span 20.79 0.23 0.63

12/15/2008 2:34:59 PM - ZERO 14.87 0.09 3.47

12/15/2008 2:35:29 PM - Span 0.2 0.06 4.72

12/15/2008 2:35:59 PM - ZERO 0.08 0.04 3.99

12/15/2008 2:36:29 PM - ZERO 0.06 0.03 3.98

12/15/2008 2:36:59 PM - ZERO 5.58 0.02 2.97

12/15/2008 2:37:29 PM - ZERO 5.14 3.01 2.75

12/15/2008 2:37:59 PM - ZERO 19.94 0.32 0.62

12/15/2008 2:38:29 PM - ZERO 20.8 0.03 0.55

12/15/2008 2:38:59 PM - ZERO 20.83 0.02 -0.01

12/15/2008 2:39:29 PM - ZERO 20.85 0.02 0.01

12/15/2008 2:39:59 PM - ZERO 18.16 2.12 2.4

12/15/2008 2:40:29 PM - ZERO 12.14 8.2 3.64

12/15/2008 2:40:59 PM - ZERO 12 8.67 3.63

12/15/2008 2:41:29 PM - ZERO 17.17 4.72 0.63

12/15/2008 2:41:59 PM - ZERO 20.84 0.24 -0.07

12/15/2008 2:42:29 PM - ZERO 20.87 0.1 -0.09

Page 15 of 15
CYLINDER GAS CERTIFICATES 

rp KA'I'A CLASS iM Scott Specialty Gases Dual-Analyzed Calibration Standard 

61 41 EASTON ROAD, BLDG 1 ,PLUMSTEADVICCE,PA 1 8949-0310 Phone 800-33 1-4953 Fax: 21 5-766-7226 

CERTlFlCATE OF ACCURACY : EPA Protocol Gas 

Assay Laboratory Customer 

P.O. NO.: E-NO6925 TAMPA ELECTRIC COMPANY 

SCOTT SPECIALTY GASES Project No.: 01 -5867 1 -002 CHARLES DUFENY 

6141 EASTON ROAD, BLDG 1 501 0 CAUSEWAY BLVD 

PLUMSTEADVILLE,PA 18949-03 1 0 TAMPA FL 3361 9 

ANALYTICAL INFORMATION 

This certificat~ov was performed according to €PA Traceabll~ty Protocol For Assay & Cerul~cat~on ofGaseous Calibrat~on Standards; 

Procedure G-1 ; Sapteniber, 1997. 

Cylinder Number: ALM0220 18 Certification Date: 120ct2006 Exp. Date: 1 10ct2009 

Cylinder Pressure* * *: 2000 PSlG 

ANALYTICAL 

COMPONENT CERTIFIED CONCENTRATION (Moles) ACCURACY* * TRACEABILITY 

CARBON DIOXIDE 18.0 % +/- 1% Direct NtST and NMi 

OXYGEN 20.9 % +I- 1% Direct NET and NMi 

NITROGEN BALANCE 

*"' Do not u~e when c {l~ndur pressure 1s below 150 psig 

'" Analyt~cal accurdr.7 13 based on the requiremenrr ol EPA Prolocol Procedure GI. Seplemher 1997. 

REFERENCE STANDARD 

-- TYPEISRM NO. EXPIRATION DATE CYLINDER NUMBER CONCENTRATlON COMPONENT 

NTRtd 1675 05Ju12008 KOr?1509 13.93 W CARBON DIOXIDE 

MTHM 2659 04Ju12QDB KO046 10 20.85 % OXYGEN 

INSTRUMENTATION 

INSTRUMEN-T/MODEL/SERlA~+ -- DATE LAST CALIBRATED ANALYTICAL PRINCIPLE 

MT I!M200/170927 ZOSep2006 GC-TCD 

MTI!M?00/170927 20Sep2006 GC-TCD 

ANALYZER READINGS 

(Z =Zero Gas R = Reference Gas T = Test Gas r =Correlation Coefficient) 

First Triad Analysis Second Triad Analysis Calibration Curve 

Concsntratlon= A+ 0a +C#2+ 0x3 + Ex4 

21 =0.00000 R1=643255 0 TI = 826324.0 

R2 =643437.0 ZZ = 0,00000 T2 - 826277.0 

23 = 0,00000 T3- 826351 0 U3 = 643355.0 8 = 2.1 778E.05 

Avg. Concentration 

OXY GEM 

Canctwltration- At Bx +Crt t 0x3 + Ex4 

2 1 = 0 00000 A1 = 536286.0 TI = 549300.0 

R2 = 636629 0 22=0.00000 T2 = 549027.0 Constants: A=1.9132E-02 

23 = 0 00000 T3 = 548522.0 A3 = 637922.0 B= 3.8059E-05 

Aug. Concentration. 

APPROVED BY: A 


APPENDIX B 

VOLATILE ORGANIC COMPOUNDS DATA 
FIELD DATA SHEETS 
LABORATORY ANALYSIS – ENTHALPY ANALYTICAL, INC 
APPENDIX C 

SULFURIC ACID MIST TEST DATA 
FIELD DATA SHEETS 






CALCULATED RUN DATA 
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 1

Date: 12/15/08

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 30.08 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 30.04 "Hg Average Orifice Meter, ΔH: 1.233 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 38.055 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 73.6 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 320.4 o

F

12.0 % O2 Average √Δp: 1.111 "H2O

0.0 % CO Condensate Volume, Vlc: 49.9 ml

79.0 % N2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.352 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.982 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.060 %

FDA = 1.0 - Bws 0.940 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.92 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.21 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 75.23 ft/second

Qs = vs x As x 60 1279774.1 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 817322.9 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 101.0 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.0101

Volume Titrant Blank, Vtb 0.02

Volume Titrant Sample, Vt 5.45

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 8.015E-07 lb/dscf

Fc-factor = 2310 dscf/mmBtu

E H2SO4 = C H2SO4 x Fc-factor x (100/%CO2) = 0.02057 lb/mmBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 39 lb/hr
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 2

Date: 12/15/08

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 30.08 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 30.03 "Hg Average Orifice Meter, ΔH: 1.292 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 39.137 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 79.0 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 320.9 o

F

12.0 % O2 Average √Δp: 1.133 "H2O

0.0 % CO Condensate Volume, Vlc: 44.8 ml

79.0 % N2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.112 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 37.657 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.053 %

FDA = 1.0 - Bws 0.947 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.92 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.29 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 76.64 ft/second

Qs = vs x As x 60 1303698.2 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 837812.4 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 100.3 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.0101

Volume Titrant Blank, Vtb 0.02

Volume Titrant Sample, Vt 8.55

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 1.237E-06 lb/dscf

Fc-factor = 2310 dscf/MMBtu

E H2SO4 = C H2SO4 x Fc-factor x (100/%CO2) = 0.03174 lb/MMBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 62 lb/hr
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 3

Date: 12/15/08

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 30.02 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 29.97 "Hg Average Orifice Meter, ΔH: 1.306 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 39.522 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 73.4 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 322.0 o

F

12.0 % O2 Average √Δp: 1.136 "H2O

0.0 % CO Condensate Volume, Vlc: 48.3 ml

79.0 % N2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.277 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 38.356 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.056 %

FDA = 1.0 - Bws 0.944 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.92 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.25 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 77.06 ft/second

Qs = vs x As x 60 1310862.0 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 836818.8 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 102.3 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.0101

Volume Titrant Blank, Vtb 0.02

Volume Titrant Sample, Vt 6.8

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 9.650E-07 lb/dscf

Fc-factor = 2310 dscf/MMBtu

E H2SO4 = C H2SO4 x Fc-factor x (100/%CO2) = 0.02477 lb/MMBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 49 lb/hr
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 4

Date: 12/16/08

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 30.00 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 29.95 "Hg Average Orifice Meter, ΔH: 1.218 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 38.361 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 77.0 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 320.0 o

F

12.0 % O2 Average √Δp: 1.101 "H2O

0.0 % CO Condensate Volume, Vlc: 46.1 ml

79.0 % N2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.173 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.945 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.056 %

FDA = 1.0 - Bws 0.944 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.92 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.26 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 74.60 ft/second

Qs = vs x As x 60 1269064.4 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 812109.4 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs x 60) 101.6 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.0101

Volume Titrant Blank, Vtb 0.02

Volume Titrant Sample, Vt 3.82

Volume of Sample Aliquot, Va 50

Total Volume of Solution, Vsoln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 5.615E-07 lb/dscf

Fc-factor = 2310 dscf/MMBtu

E H2SO4 = C H2SO4 x Fc-factor x (100/%CO2) = 0.01441 lb/MMBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 27 lb/hr
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 5

Date: 12/16/08

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 30.00 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 29.95 "Hg Average Orifice Meter, ΔH: 1.230 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 38.735 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 87.8 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 322.2 o

F

12.0 % O2 Average √Δp: 1.097 "H2O

0.0 % CO Condensate Volume, Vlc: 42.7 ml

79.0 % N2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.013 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.569 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.052 %

FDA = 1.0 - Bws 0.948 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.92 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.30 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 74.40 ft/second

Qs = vs x As x 60 1265685.7 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 810552.2 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs 100.7 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.0101

Volume Titrant Blank, Vtb 0.02

Volume Titrant Sample, Vt 5.25

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 7.807E-07 lb/dscf

Fc-factor = 2310 dscf/MMBtu

E H2SO4 = C H2SO4 x Fc-factor x (100/%CO2) = 0.02004 lb/MMBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 38 lb/hr
Environmental Services

Air Services Group

40 CFR 60, Appendix A - Test Methods

Reference Method 8

Test Calculations

Customer: Polk Power Station

Facility: Unit 1

Sampling Location: Stack

Operating Conditions: Full Load

Run Number: 6

Date: 12/16/08

Sample Time, θ: 60 minutes Nozzle Diameter, Dn: 0.197 inches

Barometric Pressure, Pb: 30.00 "Hg Nozzle Area, An: 0.00021166 ft2

Stack Pressure, Ps: 29.95 "Hg Average Orifice Meter, ΔH: 1.259 "H2O

Effective Stack Area, As: 283.529 ft2 Sample Volume, Vm: 39.723 ft3

Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., Tm: 98.5 o

F

Gas Analysis: 9.0 % CO2 Average Stack Temp., Ts: 322.0 o

F

12.0 % O2 Average √Δp: 1.099 "H2O

0.0 % CO Condensate Volume, Vlc: 47.8 ml

79.0 % N2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements:

Vw(std) = 4.714E-02 x Vlc 2.253 scf

Vm(std) = 17.647 x Vm x Y x (Pb + (ΔH / 13.6)) / (Tm +460) 36.791 dscf

Bws = Vw(std) / (Vm(std) + Vw(std)) 0.058 %

FDA = 1.0 - Bws 0.942 %

Md = (0.44 x %CO2) + (0.32 x %O2) + (0.28 x (%N2 + % CO)) 29.92 lb./lb. mole

Ms = (Md x FDA) + (18.0 x Bws) 29.23 lb./lb. mole

vs = 85.49 x Cp x (√Δp) x (√(Ts + 460) / (Ms x Ps)) 74.60 ft/second

Qs = vs x As x 60 1269097.6 acf/minute

Qs(std) = Qs x FDA x (528 / (Ts + 460)) x (Ps / 29.92)) 808202.2 dscf/minute

I = (Ts + 460) x ((2.67E-03 x Vlc) + (Vm(std) / 17.647)) x 100 / (θ x Ps x An x vs 101.6 %

Data from Laboratory Analysis: H2SO4

Normality of Barium Chloride titrant, N 0.0101

Volume Titrant Blank, Vtb 0.02

Volume Titrant Sample, Vt 5.48

Volume of Sample Aliquot, Va 100

Total Volume of Solution, Vsoln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (Vt

 - Vtb) x (Vsoln / Va)) / Vm(std) = 8.102E-07 lb/dscf

Fc-factor = 2310 dscf/MMBtu

E H2SO4 = C H2SO4 x Fc-factor x (100/%CO2) = 0.02079 lb/MMBtu

E H2SO4 = C H2SO4 x Qs(std) x 60 = 39 lb/hr
LABORATORY ANALYSIS 
Laboratory Services

5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272

Report For:

Laboratory ID: AA98712

Date and Time Collected:

Sampled By:

Sample Information

Description: SCOTT GIVEN

Location Code:

Report Date: 01/26/2009

Polk No. 1 Acid Mist Comp on Syngas

TE_PPS_1_SAM_SYNGAS

Project Account Code:

Sample Collection Method: Date of Sample Receipt: 12/17/2008

Laboratory Results

12/15/2008 12:00:00 AM

PARAMETER Result

Qualifier

Code

Test

Method Analyst Units

Upper

MDL Limit

Violation

Check

Analysis

Date & Time

Lower

Limit

Normality of BaCl2 * 2H2O 0.0001 KARXL 0.0101 12/17/2008 1:00:00 PM

SO3, Avg. of Blank Titrations milliliters 0.01 EPA - Meth.8 KARXL 0.02 I 12/17/2008 1:00:00 PM

SO3, Run #1, Avg. of Titrations 5.45 12/17/2008 1:00:00 PM milliliters 0.01 EPA - Meth.8 KARXL

SO3, Run #2, Avg. of Titrations 8.55 12/17/2008 1:00:00 PM milliliters 0.01 EPA - Meth.8 KARXL

SO3, Run #3, Avg. of Titrations 6.80 12/17/2008 1:00:00 PM milliliters 0.01 EPA - Meth.8 KARXL

SO3, Run #4, Avg. of Titrations 3.82 12/17/2008 1:00:00 PM milliliters 0.01 EPA - Meth.8 KARXL

SO3, Run #5, Avg. of Titrations 5.25 12/17/2008 1:00:00 PM milliliters 0.01 EPA - Meth.8 KARXL

SO3, Run #6, Avg. of Titrations 5.48 12/17/2008 1:00:00 PM milliliters 0.01 EPA - Meth.8 KARXL

SO3, Volume of Contained Sample milliliters 1 EPA - Meth.8 KARXL see comment 12/17/2008 1:00:00 PM

SO3, Volume of Sample Aliquot milliliters 0.1 EPA - Meth.8 KARXL see comment 12/17/2008 1:00:00 PM

Comments

Ray McDarby,

Manager, Laboratory Services

I - The reported value is between the laboratory method detection limit (MDL) and the laboratory practical quantitation limit (PQL). PQL = 4 x MDL.

All results calculated on a wet to wet basis, unless otherwise indicated.

Data Qualifier Codes Explanation:

Should there be any questions regarding this report, please contact:

(813) 630-7878

For Peggy Penner,

Report Number: Page 1 of 1 "General Report" AA98712-012609-19

All of the results presented in this report pertain to results for sample AA98712
EQUIPMENT CALIBRATIONS 
Environmental Services

Air Services Group

SUMMARY OF EQUIPMENT CALIBRATIONS

EQUIPMENT CAL DATE METHOD RESULTS

CONSOLE (MB 07) USEPA RM 5

INITIAL 10/24/2008 (ORIFICE) 0.974

POST TEST 12/17/2008 0.986

NOZZLE (SN16) CALIPER 

INITIAL 10/24/2008 MEASUREMENTS 0.197

POST TEST 12/17/2008 0.198

PYROMETER (PY 09) 10/24/2008 ASTM THERMOMETER + 2o

 F

PITOT TUBE (PT 11) 10/24/2008 USEPA RM 2 Cp = 0.84

BAROMETER (BR 06) 12/05/2008 NWS COMPARISON + 0.01" Hg
Environmental Services

Air Services Group

Blue Team

Manufacturer: Thermo Anderson Calibration Date:

Model Number:MST-C1 Barometric Pressure: 29.93 "Hg

Instrument Code Number: ^MB07 Theoretical Critical Vacuum: 14.12 "Hg

LabWorks Sample Number: Calibrated By:

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

0.63 15 130.700 137.750 7.050 79 74 80 75

1.15 15 154.500 163.894 9.394 86 77 85 78

1.90 15 141.910 153.917 12.007 83 75 86 77

3.55 15 164.650 181.150 16.500 86 79 94 81

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

48 0.3448 23.0 72 72 72.0

55 0.4593 21.5 72 72 72.0

63 0.5917 19.5 72 72 72.0

73 0.8101 16.5 72 72 72.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

6.942 6.711 6.763 0.967 -0.007 1.741 -0.019

9.185 8.940 9.008 0.973 0.000 1.776 0.016

11.789 11.517 11.605 0.977 0.003 1.772 0.012

16.124 15.768 15.889 0.978 0.004 1.751 -0.009

Averages: 0.974 1.760

Review/Approval:

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

29-Oct-08

Critical Orifice Readings

Ambient Temperatures

CALCULATED DATA

Critical Orifice

The Critical Orifice Coefficient, K', should be in English units.

IMPORTANT

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

10/24/2008

GDB

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

Quarterly Calibration
Environmental Services

Air Services Group

Manufacturer: THERMO Calibration Date:

Model Number:MST Barometric Pressure: 30.26 "Hg

Instrument Code Number: MB07 Theoretical Critical Vacuum: 14.27 "Hg

LabWorks Sample Number: Calibrated By:

Associated Test: Team: BLUE

Initial Final Total

ΔH Time Volume Volume Volume Inlet Outlet Inlet Outlet

"H2O Minutes ft3 ft3 ft3

oF oF oF oF

1.1 10 847.200 853.335 6.135 76 72 76 71

1.1 10 853.335 859.460 6.125 76 71 77 71

1.1 10 859.460 865.575 6.115 77 72 77 72

Orifice K' Actual

Serial Orifice Vacuum Initial Final Average

Number Coefficient "Hg oF oF oF

55 0.4596 20.5 68 68 68.0

55 0.4596 20.5 68 68 68.0

55 0.4596 20.5 68 68 68.0

Dry Gas Meter Calibration Calibration

Volume Volume Volume Y ΔHα

Corrected Corrected Nominal Value QA/QC Value QA/QC

Vm(std), ft3 Vcr(std), ft3 Vcr(std), ft3 (ratio) + 0.02 "H2O + 0.2

6.152 6.052 5.987 0.984 -0.002 1.690 0.001

6.142 6.052 5.987 0.985 0.000 1.690 0.001

6.123 6.052 5.987 0.988 0.003 1.687 -0.002

Averages: 0.986 1.689

Prior Y: 0.974

% Difference:(+/-5%) -1.22% PASS

Review/Approval: Date: 5-Jan-09

CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02.

For Calibration ΔHα, the acceptable tolerance of individual values from the average is + 0.2.

Critical Orifice

USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

SEG

12/17/2008

POST - TEST CALIBRATION CHECK

Ambient Temperatures

Dry Gas Meter Readings

Initial Temperatures Final Tempertures

Critical Orifice Readings

POLK SAP-UNIT 1

IMPORTANT

IMPORTANT

For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above.

The Critical Orifice Coefficient, K', should be in English units.
Calibration Date: Responsible Party:

Nozzle Maximum Average

I.D. D1 D2 D3 Difference, "Dn, inches

^SN01 0.110 0.110 0.119 0.004 0.113

^SN04 0.121 0.121 0.120 0.000 0.121

^SN05 0.147 0.147 0.145 0.001 0.146

^SN06 0.197 0.196 0.195 0.001 0.196

^SN09 0.270 0.270 0.271 0.000 0.270

^SN10 0.294 0.295 0.296 0.001 0.295

^SN12 0.387 0.386 0.388 0.001 0.387

^SN15 0.163 0.164 0.163 0.000 0.163

^SN16 0.198 0.197 0.197 0.000 0.197

^SN19 0.278 0.280 0.279 0.001 0.279

^SN22 0.366 0.366 0.367 0.000 0.366

^SN30 0.311 0.310 0.312 0.001 0.311

^SN36 0.184 0.184 0.182 0.001 0.183

^SN37 0.210 0.209 0.209 0.000 0.209

^SN38 0.252 0.250 0.252 0.001 0.251

^SN46 0.189 0.188 0.187 0.001 0.188

^SN47 0.203 0.204 0.203 0.000 0.203

^SN48 0.252 0.252 0.251 0.000 0.252

^SN50 0.309 0.311 0.312 0.001 0.311

^SN58 0.243 0.246 0.246 0.001 0.245

^SN68 0.252 0.250 0.250 0.001 0.251

^SN69 0.371 0.370 0.374 0.002 0.372

^SN70 0.616 0.614 0.614 0.001 0.615

^SN71 0.614 0.614 0.612 0.001 0.613

^SN72 0.372 0.372 0.373 0.000 0.372

^SN73 0.510 0.510 0.509 0.000 0.510

^SN74 0.483 0.482 0.482 0.000 0.482

QA/QC Review by: 29-Oct-08

Nozzle Diameter, Dn (in)

QUARTERLY NOZZLE CALIBRATIONS

STEEL NOZZLE SET

10/24/2008 RN/JV
Environmental Services

Air Services Group

Shared Resource

Calibration Date:

Calibration Personnel:

Test Designation:

Maximum Average

D1 D2 D3 Difference, " Dn, inches

0.197 0.198 0.198 0.001 0.198

Data Notations: 

Maximum Difference must be < 0.004".

Quarterly (pre-test) value for nozzle ID SN16 was 0.197

Difference (Pre-test/Post-test) is: -0.001 PASS

QA/QC Review by: 5-Jan-09

SN16

POST TEST NOZZLE CALIBRATION 

Nozzle

Identifier

Nozzle Diameter, Dn (in)

12/17/2008

SEG

POLK 1-SAM
Environmental Services

Air Services Group

Blue Team

Pyrometer Under Test

Pyrometer Number: ^PY09

Labworks Sample #

Calibration Date: 10/24/2008

Calibrator Information

Calibrator Type/Manufacturer: Hart Scientific

Calibrator Serial Number: AOA024

Date of Last Calibration: 04/28/2008

Calibration Personnel (Typed and Signature):

Calibration Data

Calibration Reference Pyrometer

Point Temperature Indication Difference

1 400 402 -2

2 212 214 -2

3 32 33 -1

Reference temperatures must encompass the expected range of measurement. These three points

should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit.

Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration

Point Difference

1 Pass

2 Pass

3 Pass

Reviewer:

0

Varino

Pyrometer Calibration

29-Oct-08
Pitot Tube ID #

Calibration Date Operating Quarter/Year: 4-08

Openings Damaged? ___ Y ___N Repaired? ____Y ___ N ___ N/A

Labworks #:

Alpha and Beta Angle Determinations Acceptable Limits:

α 1 1.4 degrees Dt 0.48 < Dt > 0.95 cm

α 2 1.5 degrees α < 10 degrees

β 1 0.7 degrees

β 2 0.4 degrees

β1 < 5 degrees (alongside top impact openings)

Gamma, Theta, Α, Ζ, and W Determinationsβ2 < 5 degrees (alongside bottom impact openings)

ψ 0.2 degrees Ζ < 0.32 cm (Αsinψ)

Α 2.37 cm W < 0.08 cm (Asinο)

Ζ 0.008 cm Α distance between tips

ο angle of plane on side of pitots

ο 1.7 degrees ψ angle between tips

W 0.070 cm

Comments:

Calibrated by:

Quality Assurance Review / Approval: 29-Oct-08

details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems:

Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.

REMOVABLE

Pass

NOTES

All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, 

Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement

Pass

Pass (α1 measured across top impact openings)

Pass (α2 measured across bottom impact openings)

Shared Resource

0

Pass

Pass

PITOT TUBE CALIBRATION

DATA SHEET

PT11

10/24/2008
Environmental Services

Air Services Group

Blue Team

Instrument Number:

Calibration Date:

Calibration Personnel:

Labworks #:

Difference

Time "Hg

11:00 -0.01

12:00 0

13:00 0

Average Difference: -0.00333

Note: Barometric readings must agree within ± 0.1 "Hg.

Current Reference is National Weather Service, TIA.

Comments (Note any adjustments):

QA/QC Review by: Date: 5-Dec-08

Current Conditions at Tampa International Airport

30.19 30.19

30.21 30.22

30.20 30.20

Barometer Reading Reference Reading

Inches Mercury Inches Mercury

BAROMETER CALIBRATION

^BR06

12/05/2008

SEG
APPENDIX D 

TURBINE DATA 
PI Ops Data Run 1

Plant Information Source: polk-1pisrv

Start Time: 12/15/2008 9:46

End Time: 12/15/2008 11:04

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 173.0594743 6760.14281 71.7420986 2.82809007

15-Dec-08 09:46:00 173.0626984 6759.94385 68.597702 2.82734466

15-Dec-08 09:47:00 173.2358551 6767.25293 68.6590958 2.82736373

15-Dec-08 09:48:00 173.4090118 6777.07959 68.4141541 2.8273828

15-Dec-08 09:49:00 173.5586243 6757.37695 68.4911499 2.82740211

15-Dec-08 09:50:00 172.7401886 6728.31152 68.5681458 2.82742119

15-Dec-08 09:51:00 172.0959778 6734.30322 68.6451416 2.82744026

15-Dec-08 09:52:00 172.40242 6734.11816 68.8714294 2.82745934

15-Dec-08 09:53:00 172.5999756 6737.15869 69.0018921 2.82747841

15-Dec-08 09:54:00 173.3674164 6750.79541 69.0018921 2.82749748

15-Dec-08 09:55:00 173.2668457 6755.28076 69.0018921 2.82751679

15-Dec-08 09:56:00 173.4589691 6735.10107 69.0018921 2.82753587

15-Dec-08 09:57:00 173.2593384 6745.36816 69.3312225 2.82755494

15-Dec-08 09:58:00 173.75914 6759.8457 69.3824158 2.82757401

15-Dec-08 09:59:00 173.6784058 6774.84912 69.433609 2.82759309

15-Dec-08 10:00:00 172.9620209 6750.18066 69.4847946 2.82761216

15-Dec-08 10:01:00 173.9638824 6774.19824 69.5359879 2.82763147

15-Dec-08 10:02:00 173.6444397 6778.63232 69.5871811 2.82765055

15-Dec-08 10:03:00 172.0343018 6729.12646 69.3434753 2.82766962

15-Dec-08 10:04:00 172.4185333 6740.58887 69.4987411 2.82768869

15-Dec-08 10:05:00 172.8027649 6746.29688 69.3264389 2.82770777

15-Dec-08 10:06:00 172.9741821 6747.9585 69.4026184 2.82772684

15-Dec-08 10:07:00 172.5327759 6791.24561 69.4787979 2.82774615

15-Dec-08 10:08:00 172.9446106 6791.55762 69.5549774 2.82776523

15-Dec-08 10:09:00 172.8365326 6747.40186 69.6311569 2.8277843

15-Dec-08 10:10:00 172.7392731 6763.67139 69.7073364 2.82780337

15-Dec-08 10:11:00 172.7933197 6774.20898 69.7835159 2.82782245

15-Dec-08 10:12:00 172.1694031 6762.30859 69.8596954 2.82784152

15-Dec-08 10:13:00 171.9230499 6740.47266 69.9358749 2.82786083

15-Dec-08 10:14:00 172.055954 6735.87695 70.0120544 2.82787991

15-Dec-08 10:15:00 172.859436 6753.11133 70.0882339 2.82789898

15-Dec-08 10:16:00 173.3289948 6770.34521 70.1644135 2.82791805

15-Dec-08 10:17:00 174.1051636 6780.58789 70.240593 2.82793713

15-Dec-08 10:18:00 173.4714203 6767.16846 70.4164658 2.8279562

15-Dec-08 10:19:00 173.3071747 6759.58887 70.2612 2.82797551

Page 1 of 3
PI Ops Data Run 1

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

15-Dec-08 10:20:00 172.1000519 6747.9707 70.6729202 2.82799459

15-Dec-08 10:21:00 171.7844238 6733.9585 70.8046036 2.82801366

15-Dec-08 10:22:00 172.6538696 6755.76367 70.9362946 2.82803273

15-Dec-08 10:23:00 173.2496796 6768.34668 71.0679779 2.82805181

15-Dec-08 10:24:00 173.7445374 6785.41553 71.1996613 2.82807088

15-Dec-08 10:25:00 174.1471405 6774.04883 71.3313522 2.82809019

15-Dec-08 10:26:00 172.9082794 6769.0376 71.4630356 2.82810926

15-Dec-08 10:27:00 172.9929352 6772.7041 71.4981537 2.82812834

15-Dec-08 10:28:00 173.1842957 6732.05762 71.8919983 2.82814741

15-Dec-08 10:29:00 172.2243195 6723.48584 72.0046463 2.82816648

15-Dec-08 10:30:00 173.2681732 6744.98877 72.1172867 2.82818556

15-Dec-08 10:31:00 173.9848938 6783.70459 72.2299271 2.82820463

15-Dec-08 10:32:00 173.9623718 6765.53564 72.3425751 2.82822394

15-Dec-08 10:33:00 173.5643311 6769.12891 72.4552155 2.82824302

15-Dec-08 10:34:00 173.3208771 6752.3291 72.5186386 2.82826209

15-Dec-08 10:35:00 172.3071442 6749.02881 72.8810959 2.82828116

15-Dec-08 10:36:00 172.4146423 6745.72852 73.003891 2.82830024

15-Dec-08 10:37:00 172.8871918 6747.66797 73.1266861 2.82831931

15-Dec-08 10:38:00 172.967804 6762.56543 73.2494736 2.82833862

15-Dec-08 10:39:00 173.0484161 6752.75049 73.3722687 2.8283577

15-Dec-08 10:40:00 172.9184875 6730.57422 73.6122818 2.82837677

15-Dec-08 10:41:00 173.0204163 6728.92236 73.5044861 2.82839584

15-Dec-08 10:42:00 173.2832336 6743.4248 73.6584854 2.82841492

15-Dec-08 10:43:00 173.407486 6744.34717 73.8124771 2.82843399

15-Dec-08 10:44:00 174.0248108 6778.74268 73.9664688 2.8284533

15-Dec-08 10:45:00 173.8222351 6757.25732 74.007988 2.82847238

15-Dec-08 10:46:00 173.1537781 6779.42334 73.8552475 2.82849145

15-Dec-08 10:47:00 173.0285034 6753.93896 73.850029 2.82851052

15-Dec-08 10:48:00 172.2003021 6742.71582 73.889473 2.8285296

15-Dec-08 10:49:00 172.7046051 6767.55859 74.3514557 2.82854867

15-Dec-08 10:50:00 172.7745972 6749.83301 74.4156189 2.82856798

15-Dec-08 10:51:00 173.5269623 6780.70801 74.5696106 2.82858706

15-Dec-08 10:52:00 173.9883423 6796.93555 74.7236023 2.82860613

15-Dec-08 10:53:00 173.2201691 6772.05371 74.877594 2.8286252

15-Dec-08 10:54:00 172.5875397 6770.23535 74.742424 2.82864428

15-Dec-08 10:55:00 172.7230682 6770.71777 74.7514114 2.82866335

15-Dec-08 10:56:00 172.6773834 6785.85254 75.1592026 2.82868266

15-Dec-08 10:57:00 173.3948822 6814.75586 75.5670013 2.82870173

15-Dec-08 10:58:00 173.7415924 6797.3999 75.9041977 2.82872081

15-Dec-08 10:59:00 172.0879211 6748.1499 75.6287231 2.82873988

Page 2 of 3
PI Ops Data Run 1

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

15-Dec-08 11:00:00 172.8661499 6769.60498 75.7852859 2.82875896

15-Dec-08 11:01:00 173.9151001 6787.28564 75.6242981 2.82877803

15-Dec-08 11:02:00 174.4136963 6791.31885 75.7264023 2.82879734

15-Dec-08 11:03:00 172.9187927 6784.37939 75.8285141 2.82881641

15-Dec-08 11:04:00 172.8209381 6747.6167 75.9306183 2.82883549

Page 3 of 3
PI Ops Data Run 2

Plant Information Source: polk-1pisrv

Start Time: 12/15/2008 11:44

End Time: 12/15/2008 12:57

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 173.005128 6768.49807 76.6046432 2.83029763

15-Dec-08 11:44:00 172.4010468 6732.06982 76.851532 2.8296001

15-Dec-08 11:45:00 173.7168121 6833.3252 76.720459 2.82961917

15-Dec-08 11:46:00 173.9635773 6757.3418 76.589386 2.82963824

15-Dec-08 11:47:00 172.8969421 6758.20215 76.458313 2.82965732

15-Dec-08 11:48:00 172.1069336 6759.0625 76.32724 2.82967639

15-Dec-08 11:49:00 172.2890472 6741.14063 76.196167 2.82969546

15-Dec-08 11:50:00 172.4711609 6716.95801 76.065094 2.82971478

15-Dec-08 11:51:00 172.6532745 6720.13525 75.934021 2.82973385

15-Dec-08 11:52:00 172.3290863 6733.26172 75.934021 2.82975292

15-Dec-08 11:53:00 172.7487335 6752.76855 76.247139 2.829772

15-Dec-08 11:54:00 173.1809998 6798.604 75.6516953 2.82979107

15-Dec-08 11:55:00 174.0948334 6777.42822 75.7902908 2.82981014

15-Dec-08 11:56:00 173.6275787 6757.62744 75.6362915 2.82982945

15-Dec-08 11:57:00 173.4067383 6789.52881 75.7325058 2.82984853

15-Dec-08 11:58:00 172.3660889 6787.30566 75.856514 2.8298676

15-Dec-08 11:59:00 173.3027191 6768.94141 75.9805222 2.82988667

15-Dec-08 12:00:00 173.2371979 6768.91162 76.1045303 2.82990575

15-Dec-08 12:01:00 173.0919189 6775.54883 76.2285385 2.82992482

15-Dec-08 12:02:00 173.8414612 6782.18604 76.1593933 2.82994413

15-Dec-08 12:03:00 173.6455231 6762.66943 76.0561676 2.82996321

15-Dec-08 12:04:00 173.100708 6764.68604 75.9529419 2.82998228

15-Dec-08 12:05:00 172.17659 6733.88477 76.0849304 2.83000135

15-Dec-08 12:06:00 172.9056396 6764.41113 76.269722 2.83002043

15-Dec-08 12:07:00 173.3415985 6787.14502 76.4545135 2.8300395

15-Dec-08 12:08:00 173.1659851 6779.71484 76.6393051 2.83005881

15-Dec-08 12:09:00 173.2914734 6765.896 76.8240967 2.83007789

15-Dec-08 12:10:00 173.0330048 6762.21094 76.76091 2.83009696

15-Dec-08 12:11:00 173.1410675 6762.21094 76.6075439 2.83011603

15-Dec-08 12:12:00 173.5596771 6762.21094 76.4541779 2.83013511

15-Dec-08 12:13:00 173.4306183 6773.76123 76.3008194 2.83015418

15-Dec-08 12:14:00 172.6535034 6742.95996 76.3798752 2.83017349

15-Dec-08 12:15:00 172.3942261 6760.01074 76.5840836 2.83019257

15-Dec-08 12:16:00 172.6193542 6749.79785 76.7882919 2.83021164

15-Dec-08 12:17:00 173.1296539 6817.91943 76.8733749 2.83023071

Page 1 of 2
PI Ops Data Run 2

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

15-Dec-08 12:18:00 173.1124268 6745.68555 76.8733749 2.83024979

15-Dec-08 12:19:00 172.324585 6762.8833 77.0171051 2.83026886

15-Dec-08 12:20:00 172.6633148 6769.1167 77.0403748 2.83028817

15-Dec-08 12:21:00 173.175293 6768.18018 76.8733749 2.83030725

15-Dec-08 12:22:00 172.8448639 6743.40039 76.8733749 2.83032632

15-Dec-08 12:23:00 173.3446655 6778.56982 77.137146 2.83034539

15-Dec-08 12:24:00 173.7305756 6767.84668 77.0350418 2.83036447

15-Dec-08 12:25:00 172.9767303 6760.98828 76.9329376 2.83038354

15-Dec-08 12:26:00 173.390976 6775.646 77.1454315 2.83040285

15-Dec-08 12:27:00 173.6652527 6795.81689 77.0427704 2.83042192

15-Dec-08 12:28:00 173.4738007 6781.96826 76.9401093 2.830441

15-Dec-08 12:29:00 172.9471588 6752.55518 76.9378433 2.83046007

15-Dec-08 12:30:00 172.3932648 6749.25488 77.1220322 2.83047915

15-Dec-08 12:31:00 173.2393951 6790.48145 77.306221 2.83049822

15-Dec-08 12:32:00 172.8953094 6748.75391 77.4904099 2.83051753

15-Dec-08 12:33:00 173.6369781 6787.76855 77.6745987 2.8305366

15-Dec-08 12:34:00 174.0136108 6789.46338 77.7742386 2.83055568

15-Dec-08 12:35:00 173.1564941 6766.98145 77.6202469 2.83057475

15-Dec-08 12:36:00 172.8784637 6762.60596 77.2481003 2.83059382

15-Dec-08 12:37:00 172.6004333 6758.22998 77.3866882 2.8306129

15-Dec-08 12:38:00 172.322403 6755.90918 76.7707138 2.83063221

15-Dec-08 12:39:00 172.0586853 6762.43506 76.5188522 2.83065128

15-Dec-08 12:40:00 172.6395416 6754.979 76.2083206 2.83067036

15-Dec-08 12:41:00 173.2203979 6747.52344 76.2558975 2.83068943

15-Dec-08 12:42:00 172.4950867 6745.09717 76.343483 2.8307085

15-Dec-08 12:43:00 173.3929291 6774.31152 76.4310684 2.83072758

15-Dec-08 12:44:00 173.1497803 6823.44678 76.5186539 2.83074689

15-Dec-08 12:45:00 172.5468597 6794.44824 76.6062393 2.83076596

15-Dec-08 12:46:00 172.8034363 6796.46484 76.6938248 2.83078504

15-Dec-08 12:47:00 172.6923065 6803.375 76.7814102 2.83080411

15-Dec-08 12:48:00 172.2337799 6822.40137 76.8689957 2.83082318

15-Dec-08 12:49:00 172.4930573 6780.27051 76.8150482 2.83084226

15-Dec-08 12:50:00 173.544281 6788.22021 76.7536545 2.83086157

15-Dec-08 12:51:00 173.772049 6793.62305 76.6922607 2.83088064

15-Dec-08 12:52:00 173.3268127 6786.28955 76.6308594 2.83089972

15-Dec-08 12:53:00 173.2579956 6778.95605 76.5694656 2.83091879

15-Dec-08 12:54:00 172.8797607 6763.5874 76.8220444 2.83093786

15-Dec-08 12:55:00 172.5119019 6718.19092 76.7032013 2.83095694

15-Dec-08 12:56:00 172.3059692 6736.69873 76.4989929 2.83097625

15-Dec-08 12:57:00 172.954071 6786.59521 76.2947845 2.83099532

Page 2 of 2
PI Ops Data Run 3

Plant Information Source: polk-1pisrv

Start Time: 12/15/2008 13:23

End Time: 12/15/2008 14:31

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 173.169507 6760.15128 76.1822533 2.83214201

15-Dec-08 13:23:00 171.5643768 6713.1123 73.8207855 2.83149219

15-Dec-08 13:24:00 173.2479401 6757.62305 73.7200775 2.83151126

15-Dec-08 13:25:00 173.6364899 6775.92627 73.5660858 2.83153033

15-Dec-08 13:26:00 173.9234924 6784.15039 73.4462891 2.83154941

15-Dec-08 13:27:00 172.8862915 6753.21826 73.4974823 2.83156872

15-Dec-08 13:28:00 173.1447144 6773.05566 73.5486755 2.83158779

15-Dec-08 13:29:00 173.6054535 6762.23828 73.5998611 2.83160686

15-Dec-08 13:30:00 171.4996796 6745.94873 73.6510544 2.83162594

15-Dec-08 13:31:00 172.6348114 6709.32178 73.7022476 2.83164501

15-Dec-08 13:32:00 173.4101868 6737.33789 73.7354813 2.83166409

15-Dec-08 13:33:00 174.4727936 6778.8335 73.4690704 2.8316834

15-Dec-08 13:34:00 173.2949066 6773.73438 74.0639954 2.83170247

15-Dec-08 13:35:00 173.6048584 6731.08008 74.2179871 2.83172154

15-Dec-08 13:36:00 173.0282135 6761.3125 74.3719864 2.83174062

15-Dec-08 13:37:00 172.9110107 6770.79102 74.5259781 2.83175969

15-Dec-08 13:38:00 173.3613892 6791.89355 74.6799698 2.83177876

15-Dec-08 13:39:00 173.8928528 6779.53809 74.4717407 2.83179808

15-Dec-08 13:40:00 173.807785 6792.21826 74.5749664 2.83181715

15-Dec-08 13:41:00 173.5557098 6791.85352 74.6781921 2.83183622

15-Dec-08 13:42:00 173.682251 6791.48877 74.377121 2.8318553

15-Dec-08 13:43:00 173.3037872 6785.84375 74.7621002 2.83187437

15-Dec-08 13:44:00 172.3973846 6750.27588 75.2240829 2.83189344

15-Dec-08 13:45:00 172.1986542 6719.93115 75.4784546 2.83191276

15-Dec-08 13:46:00 172.570282 6723.5874 75.6809311 2.83193183

15-Dec-08 13:47:00 172.5708771 6744.85498 75.8834 2.8319509

15-Dec-08 13:48:00 172.1663818 6748.87207 75.6208954 2.83196998

15-Dec-08 13:49:00 173.0457458 6767.14307 76.0592651 2.83198905

15-Dec-08 13:50:00 172.6385193 6738.35205 76.0045624 2.83200812

15-Dec-08 13:51:00 172.7263031 6747.96582 76.1077881 2.83202744

15-Dec-08 13:52:00 173.2438507 6756.34424 76.2110138 2.83204651

15-Dec-08 13:53:00 173.0811462 6753.04395 76.6249237 2.83206558

15-Dec-08 13:54:00 172.8506012 6728.63867 76.7270279 2.83208466

15-Dec-08 13:55:00 173.0730591 6746.07715 76.8291321 2.83210373

15-Dec-08 13:56:00 174.0304565 6805.3877 76.916832 2.8321228

Page 1 of 2
PI Ops Data Run 3

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

15-Dec-08 13:57:00 174.2365875 6787.3374 76.993515 2.83214211

15-Dec-08 13:58:00 173.8283386 6781.28711 77.0701981 2.83216119

15-Dec-08 13:59:00 173.4200897 6776.69434 77.1468811 2.83218026

15-Dec-08 14:00:00 173.3310852 6776.73535 77.0376358 2.83219934

15-Dec-08 14:01:00 173.4000702 6763.06641 76.9452362 2.83221841

15-Dec-08 14:02:00 173.204422 6786.04492 77.0992355 2.83223748

15-Dec-08 14:03:00 173.8883972 6801.61377 77.2532272 2.83225679

15-Dec-08 14:04:00 173.1139069 6729.26465 77.4072189 2.83227587

15-Dec-08 14:05:00 172.2709961 6723.43213 77.2452927 2.83229494

15-Dec-08 14:06:00 172.7203217 6765.58496 77.3986511 2.83231401

15-Dec-08 14:07:00 172.6657867 6798.54297 77.5520172 2.83233309

15-Dec-08 14:08:00 173.322464 6785.52588 77.7053833 2.83235216

15-Dec-08 14:09:00 173.4530334 6775.98145 77.7218323 2.83237147

15-Dec-08 14:10:00 173.6880035 6783.7998 77.5540771 2.83239055

15-Dec-08 14:11:00 174.091156 6787.2002 77.7582855 2.83240962

15-Dec-08 14:12:00 173.09935 6773.81641 77.9624939 2.83242869

15-Dec-08 14:13:00 173.7175751 6792.78223 78.1258621 2.83244777

15-Dec-08 14:14:00 172.6379242 6744.61035 78.0110474 2.83246684

15-Dec-08 14:15:00 173.6240692 6766.06104 77.7100754 2.83248615

15-Dec-08 14:16:00 173.8586578 6773.76123 77.2018967 2.83250523

15-Dec-08 14:17:00 173.2462921 6777.93555 77.3045578 2.8325243

15-Dec-08 14:18:00 173.2026062 6764.48047 77.4072266 2.83254337

15-Dec-08 14:19:00 172.9852905 6748.20361 77.2121658 2.83256245

15-Dec-08 14:20:00 172.7679749 6718.35596 77.4790878 2.83258152

15-Dec-08 14:21:00 172.5506592 6707.20459 77.5021744 2.83260083

15-Dec-08 14:22:00 172.0380859 6724.28906 77.5788574 2.83261991

15-Dec-08 14:23:00 173.2303772 6741.37354 77.6555405 2.83263898

15-Dec-08 14:24:00 173.6371155 6755.70264 77.7322235 2.83265805

15-Dec-08 14:25:00 173.4345093 6756.25244 77.8088989 2.83267713

15-Dec-08 14:26:00 173.5578308 6760.07715 77.5201492 2.8326962

15-Dec-08 14:27:00 173.7319336 6775.29199 77.5713348 2.83271551

15-Dec-08 14:28:00 173.9060364 6762.2749 77.6481781 2.83273458

15-Dec-08 14:29:00 173.488266 6744.17041 77.7250137 2.83275366

15-Dec-08 14:30:00 172.3103943 6710.54004 77.801857 2.83277273

15-Dec-08 14:31:00 171.9741211 6740.14893 77.8786926 2.83279181

Page 2 of 2
PI Ops Data Run 4

Plant Information Source: polk-1pisrv

Start Time: 12/16/2008 9:05

End Time: 12/16/2008 10:15

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 173.0486274 6747.95193 66.4618365 2.88816644

16-Dec-08 09:05:00 173.2203217 6734.36768 64.3788071 2.88393021

16-Dec-08 09:06:00 173.1763306 6736.12793 64.3984833 2.88405108

16-Dec-08 09:07:00 172.985733 6728.86768 64.6294785 2.8841722

16-Dec-08 09:08:00 173.3718414 6750.81006 64.860466 2.88429332

16-Dec-08 09:09:00 173.1413879 6742.92676 65.0914612 2.8844142

16-Dec-08 09:10:00 172.4518585 6727.82275 64.940033 2.88453531

16-Dec-08 09:11:00 172.0778351 6713.98633 65.2648315 2.88465643

16-Dec-08 09:12:00 173.492691 6739.89209 65.3086243 2.88477731

16-Dec-08 09:13:00 173.3335876 6741.35889 65.352417 2.88489842

16-Dec-08 09:14:00 173.1744995 6740.3667 65.3962097 2.88501954

16-Dec-08 09:15:00 173.0223846 6733.15527 65.4400024 2.88514042

16-Dec-08 09:16:00 172.9470673 6725.94385 65.4837952 2.88526154

16-Dec-08 09:17:00 172.8621826 6728.04834 65.5275879 2.88538265

16-Dec-08 09:18:00 172.6532745 6748.9375 65.6014175 2.88550353

16-Dec-08 09:19:00 172.9054413 6741.6709 65.9026566 2.88562465

16-Dec-08 09:20:00 172.4043121 6709.43896 66.1632843 2.88574576

16-Dec-08 09:21:00 172.6395416 6719.57813 65.8860855 2.88586664

16-Dec-08 09:22:00 172.1661987 6718.12402 66.1632309 2.88598776

16-Dec-08 09:23:00 173.2667084 6731.8374 65.8732376 2.88610888

16-Dec-08 09:24:00 173.8261108 6740.1001 66.0259781 2.88622975

16-Dec-08 09:25:00 172.5392914 6711.76904 66.1787262 2.88635087

16-Dec-08 09:26:00 172.6138 6731.31152 66.0361633 2.88647199

16-Dec-08 09:27:00 173.6668549 6750.854 65.8834152 2.88659286

16-Dec-08 09:28:00 174.0005188 6760.01074 66.4353333 2.88671398

16-Dec-08 09:29:00 172.643219 6738.00977 66.215126 2.8868351

16-Dec-08 09:30:00 172.0358124 6723.28174 66.4609985 2.88695598

16-Dec-08 09:31:00 172.2720032 6728.42725 66.4456024 2.88707709

16-Dec-08 09:32:00 172.4405975 6724.63818 66.2360001 2.88719821

16-Dec-08 09:33:00 172.5126495 6726.09277 66.496933 2.88731909

16-Dec-08 09:34:00 172.2001495 6712.11035 66.183815 2.8874402

16-Dec-08 09:35:00 172.4937592 6736.43555 66.3788757 2.88756132

16-Dec-08 09:36:00 173.1445923 6740.68799 66.2248764 2.8876822

16-Dec-08 09:37:00 173.7954407 6754.06592 66.2741547 2.88780332

16-Dec-08 09:38:00 173.6329193 6783.72852 66.3973541 2.88792443

Page 1 of 2
PI Ops Data Run 4

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

16-Dec-08 09:39:00 173.1658325 6776.94531 66.520546 2.88804531

16-Dec-08 09:40:00 173.1027985 6766.61084 66.6437378 2.88816643

16-Dec-08 09:41:00 173.2180634 6751.28369 66.7669296 2.88828754

16-Dec-08 09:42:00 173.4792328 6757.88428 66.5623093 2.88840842

16-Dec-08 09:43:00 173.3233795 6768.33447 66.665535 2.88852954

16-Dec-08 09:44:00 174.004364 6788.18408 66.7687607 2.88865066

16-Dec-08 09:45:00 173.2510529 6789.12109 67.0884933 2.88877153

16-Dec-08 09:46:00 172.7871704 6771.07227 67.027298 2.88889265

16-Dec-08 09:47:00 172.8637085 6777.18359 66.9661026 2.88901377

16-Dec-08 09:48:00 173.3022766 6783.29492 66.9049072 2.88913465

16-Dec-08 09:49:00 173.2372437 6770.83691 66.8437119 2.88925576

16-Dec-08 09:50:00 172.6357117 6725.67725 66.9509506 2.88937688

16-Dec-08 09:51:00 173.1499329 6744.81787 66.943512 2.88949776

16-Dec-08 09:52:00 173.1033936 6738.31543 67.0590057 2.88961887

16-Dec-08 09:53:00 174.0241699 6762.89551 66.905014 2.88973999

16-Dec-08 09:54:00 173.510849 6758.64209 66.9262085 2.88986087

16-Dec-08 09:55:00 172.7311249 6740.35693 67.0135803 2.88998199

16-Dec-08 09:56:00 172.7129669 6747.25781 67.0205078 2.8901031

16-Dec-08 09:57:00 172.4082642 6741.22852 66.9075775 2.89022398

16-Dec-08 09:58:00 173.641922 6758.50195 67.0322647 2.8903451

16-Dec-08 09:59:00 173.7409973 6772.51465 66.8645096 2.89046621

16-Dec-08 10:00:00 173.6847076 6769.65479 67.068718 2.89058709

16-Dec-08 10:01:00 172.9918823 6756.0332 67.2729263 2.89070821

16-Dec-08 10:02:00 173.6323242 6761.01904 67.4240189 2.89082932

16-Dec-08 10:03:00 172.5830841 6739.93506 67.3626175 2.8909502

16-Dec-08 10:04:00 173.4081573 6757.05322 67.3012238 2.89107132

16-Dec-08 10:05:00 173.6329193 6769.95996 67.2398224 2.89119244

16-Dec-08 10:06:00 173.0835876 6738.47461 67.1784286 2.89131355

16-Dec-08 10:07:00 172.534256 6746.51953 67.1539688 2.89143443

16-Dec-08 10:08:00 174.0201569 6806.93799 67.410202 2.89155555

16-Dec-08 10:09:00 173.8599701 6786.28174 67.4154205 2.89167666

16-Dec-08 10:10:00 173.6718903 6765.625 67.4414291 2.89179754

16-Dec-08 10:11:00 173.4837952 6754.48633 67.5440903 2.89191866

16-Dec-08 10:12:00 172.9342957 6759.54639 67.6467514 2.89203978

16-Dec-08 10:13:00 172.351944 6742.70361 67.7494125 2.89216065

16-Dec-08 10:14:00 171.7695923 6741.05322 67.9098511 2.89228177

16-Dec-08 10:15:00 172.3046112 6743.55908 67.7545853 2.89240289

Page 2 of 2
PI Ops Data Run 5

Plant Information Source: polk-1pisrv

Start Time: 12/16/2008 10:49

End Time: 12/16/2008 11:57

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 173.0510785 6763.43727 69.452557 2.90063334

16-Dec-08 10:49:00 173.7049713 6757.02881 68.036911 2.89651799

16-Dec-08 10:50:00 173.1466217 6734.66113 68.3518295 2.89663911

16-Dec-08 10:51:00 172.6369171 6734.47754 68.2497253 2.89676023

16-Dec-08 10:52:00 172.5648804 6729.94336 68.1476212 2.8968811

16-Dec-08 10:53:00 172.4477997 6720.58057 68.1138611 2.89700222

16-Dec-08 10:54:00 171.8087769 6730.84766 68.1035995 2.89712334

16-Dec-08 10:55:00 173.230072 6736.8125 68.3667068 2.89724422

16-Dec-08 10:56:00 173.0995026 6730.94531 68.2900238 2.89736533

16-Dec-08 10:57:00 172.9689178 6741.70117 68.2133408 2.89748645

16-Dec-08 10:58:00 172.3029785 6781.64502 68.1366577 2.89760733

16-Dec-08 10:59:00 173.2269287 6772.03809 68.0727997 2.89772844

16-Dec-08 11:00:00 173.6373901 6765.41357 68.3807831 2.89784956

16-Dec-08 11:01:00 174.005127 6792.86523 68.6887741 2.89797044

16-Dec-08 11:02:00 174.5043182 6799.31885 68.5866699 2.89809155

16-Dec-08 11:03:00 174.526474 6792.10742 68.4845657 2.89821267

16-Dec-08 11:04:00 172.8135071 6787.4873 68.3824615 2.89833355

16-Dec-08 11:05:00 172.6556549 6761.13525 68.6631088 2.89845467

16-Dec-08 11:06:00 172.4679565 6760.39355 68.5476151 2.89857578

16-Dec-08 11:07:00 172.0785675 6768.70508 68.3936234 2.89869666

16-Dec-08 11:08:00 173.440506 6777.0166 68.5553131 2.89881778

16-Dec-08 11:09:00 173.3253021 6777.00049 68.4013214 2.89893889

16-Dec-08 11:10:00 172.5247955 6754.08301 68.8889618 2.89905977

16-Dec-08 11:11:00 173.5427246 6744.02393 68.4904633 2.89918089

16-Dec-08 11:12:00 173.3732605 6762.52881 68.4463577 2.89930201

16-Dec-08 11:13:00 173.1060944 6762.34521 68.615715 2.89942288

16-Dec-08 11:14:00 173.0025482 6769.23193 68.6066437 2.899544

16-Dec-08 11:15:00 173.8223419 6784.50391 68.4629211 2.89966512

16-Dec-08 11:16:00 173.8727722 6772.25781 68.4484329 2.899786

16-Dec-08 11:17:00 173.2303925 6775.55811 68.5499878 2.89990711

16-Dec-08 11:18:00 173.140625 6778.8584 68.651535 2.90002823

16-Dec-08 11:19:00 172.9582672 6774.14014 68.4904633 2.90014911

16-Dec-08 11:20:00 172.7511292 6754.99951 68.498848 2.90027022

16-Dec-08 11:21:00 172.7921143 6756.83301 68.5594406 2.90039134

16-Dec-08 11:22:00 172.3786163 6758.6665 68.8657532 2.90051222

Page 1 of 2
PI Ops Data Run 5

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

16-Dec-08 11:23:00 172.8485413 6768.71338 69.1720657 2.90063334

16-Dec-08 11:24:00 174.1778259 6797.53467 69.1480103 2.90075445

16-Dec-08 11:25:00 174.1241608 6797.3877 69.2752304 2.90087533

16-Dec-08 11:26:00 173.0505676 6755.875 69.1982346 2.90099645

16-Dec-08 11:27:00 172.5822906 6759.55273 69.1212387 2.90111756

16-Dec-08 11:28:00 172.471756 6808.5957 69.0442429 2.90123844

16-Dec-08 11:29:00 173.025589 6814.55469 69.1837006 2.90135956

16-Dec-08 11:30:00 173.0989075 6791.04785 69.0939102 2.90148067

16-Dec-08 11:31:00 172.2659912 6753.31299 69.3239594 2.90160155

16-Dec-08 11:32:00 172.5551147 6766.17139 69.5540085 2.90172267

16-Dec-08 11:33:00 173.4714203 6788.44092 69.7840576 2.90184379

16-Dec-08 11:34:00 172.9902496 6772.01367 69.8421021 2.90196466

16-Dec-08 11:35:00 172.3163452 6751.33643 69.971199 2.90208578

16-Dec-08 11:36:00 173.1473694 6765.55762 70.0710068 2.9022069

16-Dec-08 11:37:00 172.5144196 6779.7793 70.1708145 2.90232778

16-Dec-08 11:38:00 173.3349915 6785.31787 70.1720276 2.90244889

16-Dec-08 11:39:00 172.5695343 6758.64209 70.0073624 2.90257001

16-Dec-08 11:40:00 172.4838257 6739.74561 70.3125 2.90269089

16-Dec-08 11:41:00 173.0353851 6773.43115 70.61763 2.902812

16-Dec-08 11:42:00 173.1161041 6769.95898 70.819725 2.90293312

16-Dec-08 11:43:00 173.1968231 6771.10254 70.8872223 2.903054

16-Dec-08 11:44:00 173.2775421 6751.70752 70.9893341 2.90317512

16-Dec-08 11:45:00 173.3582611 6755.02393 71.0914383 2.90329623

16-Dec-08 11:46:00 174.0246582 6754.33936 71.1589432 2.90341711

16-Dec-08 11:47:00 172.9022827 6775.26465 71.1799011 2.90353823

16-Dec-08 11:48:00 171.7495728 6760.96436 71.07724 2.90365934

16-Dec-08 11:49:00 173.0628357 6746.66357 70.9745712 2.90378022

16-Dec-08 11:50:00 172.5990906 6740.6748 70.8719101 2.90390134

16-Dec-08 11:51:00 173.0673828 6747.94629 71.1850357 2.90402246

16-Dec-08 11:52:00 172.8671722 6737.07617 71.7804718 2.90414333

16-Dec-08 11:53:00 173.1305695 6750.94238 71.8112717 2.90426445

16-Dec-08 11:54:00 172.6837921 6755.92822 71.8112717 2.90438557

16-Dec-08 11:55:00 173.135376 6746.27246 71.8112717 2.90450644

16-Dec-08 11:56:00 173.8017731 6750.30615 72.4182358 2.90462756

16-Dec-08 11:57:00 173.3980408 6735.83447 72.5524521 2.90474868

Page 2 of 2
PI Ops Data Run 6

Plant Information Source: polk-1pisrv

Start Time: 12/16/2008 12:13

End Time: 12/16/2008 13:20

Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 172.9492529 6753.67327 75.5018634 2.91073994

16-Dec-08 12:13:00 172.9847107 6750.60742 73.9151382 2.90668511

16-Dec-08 12:14:00 172.5476227 6748.65625 73.9048691 2.90680623

16-Dec-08 12:15:00 172.252243 6750.57178 73.9057159 2.90692735

16-Dec-08 12:16:00 172.6333008 6740.85498 74.2153931 2.90704823

16-Dec-08 12:17:00 172.9078369 6751.55762 74.5250778 2.90716934

16-Dec-08 12:18:00 173.0861511 6805.77246 74.2792664 2.90729046

16-Dec-08 12:19:00 173.3182068 6776.62158 73.8761215 2.90741134

16-Dec-08 12:20:00 172.8448029 6751.23486 74.377121 2.90753245

16-Dec-08 12:21:00 172.7679901 6747.07129 74.377121 2.90765357

16-Dec-08 12:22:00 173.7817993 6779.8584 74.289856 2.90777445

16-Dec-08 12:23:00 173.961319 6782.26367 74.4797821 2.90789557

16-Dec-08 12:24:00 171.736969 6753.87354 74.7877655 2.90801668

16-Dec-08 12:25:00 171.9862976 6755.94678 74.910965 2.90813756

16-Dec-08 12:26:00 171.9628601 6734.44287 74.777504 2.90825868

16-Dec-08 12:27:00 172.6670837 6747.23145 74.922554 2.90837979

16-Dec-08 12:28:00 172.8201752 6754 74.7141266 2.90850067

16-Dec-08 12:29:00 173.5559235 6750.03223 74.8165131 2.90862179

16-Dec-08 12:30:00 174.0767365 6755.6748 74.9188919 2.9087429

16-Dec-08 12:31:00 173.7365875 6766.4917 75.0212708 2.90886378

16-Dec-08 12:32:00 173.9820557 6764.31934 75.1236572 2.9089849

16-Dec-08 12:33:00 171.7698517 6721.60303 75.2260361 2.90910602

16-Dec-08 12:34:00 172.0490112 6716.95557 75.3514099 2.90922689

16-Dec-08 12:35:00 172.9187927 6726.23975 75.5601501 2.90934801

16-Dec-08 12:36:00 172.2627563 6718.97949 75.0118637 2.90946913

16-Dec-08 12:37:00 172.8430023 6743.80371 75.1139679 2.90959001

16-Dec-08 12:38:00 173.3803253 6773.51709 75.2160721 2.90971112

16-Dec-08 12:39:00 173.8846283 6763.72656 75.3112564 2.90983224

16-Dec-08 12:40:00 172.2249146 6736.59229 75.3164749 2.90995312

16-Dec-08 12:41:00 172.5871124 6731.75195 75.1637344 2.91007423

16-Dec-08 12:42:00 173.2480927 6746.77051 75.010994 2.91019535

16-Dec-08 12:43:00 173.3882751 6765.81299 75.3886566 2.91031623

16-Dec-08 12:44:00 173.0418701 6764.67773 75.7942429 2.91043735

16-Dec-08 12:45:00 173.1178284 6752.67725 76.1998215 2.91055846

16-Dec-08 12:46:00 173.3208313 6749.20605 76.247139 2.91067934

Page 1 of 2
PI Ops Data Run 6

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

16-Dec-08 12:47:00 173.5238495 6766.23193 76.247139 2.91080046

16-Dec-08 12:48:00 173.2874146 6803.18115 75.934021 2.91092157

16-Dec-08 12:49:00 173.1622314 6786.30176 76.162056 2.91104245

16-Dec-08 12:50:00 173.1442261 6751.32031 76.0599518 2.91116357

16-Dec-08 12:51:00 172.7897186 6742.74023 75.9578476 2.91128469

16-Dec-08 12:52:00 172.8140259 6753.36182 76.0122986 2.91140556

16-Dec-08 12:53:00 173.3993835 6754.61328 76.1144028 2.91152668

16-Dec-08 12:54:00 173.0188904 6747.24902 76.216507 2.9116478

16-Dec-08 12:55:00 172.7127228 6739.88477 76.0279541 2.91176867

16-Dec-08 12:56:00 172.4065399 6732.52051 76.1427689 2.91188979

16-Dec-08 12:57:00 172.6683502 6743.17969 75.9900284 2.91201091

16-Dec-08 12:58:00 173.038269 6763.54443 76.1290817 2.91213179

16-Dec-08 12:59:00 173.074585 6762.18652 75.8672867 2.9122529

16-Dec-08 13:00:00 172.7962799 6731.80762 75.6821594 2.91237402

16-Dec-08 13:01:00 172.7234955 6752.87891 75.7842636 2.9124949

16-Dec-08 13:02:00 173.2864532 6767.37158 75.8863678 2.91261601

16-Dec-08 13:03:00 172.9555511 6760.64404 76.2572403 2.91273713

16-Dec-08 13:04:00 172.2033081 6747.03027 76.4826279 2.91285801

16-Dec-08 13:05:00 172.3134766 6721.06934 76.3273621 2.91297913

16-Dec-08 13:06:00 172.3649597 6725.10303 76.2214737 2.91310024

16-Dec-08 13:07:00 172.7298279 6743.46094 76.560257 2.91322112

16-Dec-08 13:08:00 173.5077972 6758.43652 76.560257 2.91334224

16-Dec-08 13:09:00 173.690918 6763.67773 76.1208801 2.91346335

16-Dec-08 13:10:00 173.4001312 6763.67773 75.9508438 2.91358423

16-Dec-08 13:11:00 172.609787 6779.93359 75.9947433 2.91370535

16-Dec-08 13:12:00 173.4750214 6776.80469 76.0386353 2.91382647

16-Dec-08 13:13:00 173.2748108 6747.94727 76.0825348 2.91394734

16-Dec-08 13:14:00 172.264389 6749.37695 76.1264267 2.91406846

16-Dec-08 13:15:00 172.713913 6761.39209 76.1703262 2.91418958

16-Dec-08 13:16:00 172.7949677 6746.26025 76.2142181 2.91431046

16-Dec-08 13:17:00 172.5339508 6758.93555 76.4883957 2.91443157

16-Dec-08 13:18:00 174.4347076 6767.69873 76.1804123 2.91455269

16-Dec-08 13:19:00 173.0819092 6760.73193 75.9650726 2.91467357

16-Dec-08 13:20:00 172.705368 6739.83105 76.1203384 2.91479468

Page 2 of 2
APPENDIX E 

FUEL ANALYSIS 
Date/time 12/15/08 9:46 12/15/08 1

Date/time 12/16/08 8:00 12/15/08 11:04 12/15/08 1 ELEMENT Pi Tag CAL. GAS MS Actual MS Normalized Adjustment Raw Data Adjusted Data

Normalized & 

Adjusted Raw Data 

H2 1ASHYI015 36.00 36.20 36.22 1.006 33.35 33.56 32.68 3N2 1ASHYI016 3.15 3.13 3.13 0.994 3.54 3.52 3.47 CH4 1ASHYI018 0.0336 0.0328 0.0328 0.977 0.0271 0.03 0.03 0.CO 1ASHYI021 44.14 43.90 43.93 0.995 45.71 45.49 44.79 4H2S 1ASHYI019 0.6010 0.6216 0.6220 1.00 0.0207 0.02 0.02 0.CO2 1ASHYI022 15.00 15.00 15.01 1.001 15.70 15.71 15.39 1COS 1ASHYI020 0.0300 0.0204 0.0204 1.00 0.0100 0.01 0.01 0.AR 1ASHYI017 1.05 1.03 1.03 0.982 0.81 0.80 0.80 Subtotal (Dry) 100.00 99.93 100.00 1.000 99.17 99.13 97.17 9H2O 1TSYAI202 2.83 2.83 2.83 Total (Moist) 100.00 Mole Wt (Moist) 21.79 Flow (KSCFH) 1TSYFI100 6760 6622 Mole Wt (Dry) 21.90 HHV-Dry (BTU/SCF) 257.3 HHV-Moist (BTU/SCF) 250.0 HHV (MMBTU/Hr) 1656 LHV (BTU/SCF) 233.7 LHV (MMTU/Hr) 1548 SO2 (Lb/Hr) from MS 336 SO2 (Lb/Hr) from CEM 1FGOFYI906 320 HHV TO CT 1tshai200 1592 DRY GAS TO CT 1tshai201 1589 

Run 1 CALIBRATION CHECK AND ADJUSTMENT FACTORS 
12/15/08 13:23 12/16/08 9:05 12/16/08 10:49 12/16/08 12:

12/15/08 14:31 12/16/08 10:15 12/16/08 11:57 12/16/08 13:

Raw Data Adjusted Data

Normalized & Adjusted Raw Data Adjusted Data

Normalized & Adjusted Raw Data Adjusted Data

Normalized & Adjusted Raw Data 

33.37 33.58 32.78 32.99 33.19 32.38 32.97 33.18 32.31 32.

3.42 3.40 3.36 3.35 3.34 3.29 3.41 3.39 3.34 3.

0.0272 0.03 0.03 0.0282 0.03 0.03 0.0284 0.03 0.03 0.02

45.61 45.39 44.79 45.88 45.67 45.04 45.90 45.68 44.97 45.

0.0223 0.02 0.02 0.0231 0.02 0.02 0.0223 0.02 0.02 0.02

15.66 15.67 15.38 15.83 15.84 15.54 15.93 15.94 15.61 15.

0.0106 0.01 0.01 0.0110 0.01 0.01 0.0110 0.01 0.01 0.01

0.82 0.80 0.80 0.82 0.81 0.81 0.82 0.81 0.81 0.

98.93 98.90 97.17 98.94 98.90 97.11 99.09 99.06 97.10 98.

2.83 2.83 2.83 2.89 2.89 2.89 2.90 2.90 2.90 2.

100.00 100.00 100.00 

21.77 21.89 21.92 

6761 6627 6748 6595 6764 6607 67

21.87 22.00 22.03 257.7 257.3 256.9 250.4 249.9 249.5 

1659 1648 1648 

234.0 233.7 233.3 

1551 1541 1541 

360 371 364 328 336 328 

1595 1591 1596 1591 1589 1591 

Run 3 Run 4 Run 5 
APPENDIX F 

CEMS DATA 
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 9:46 37.38 17.6 8.7 10.7 799

12/15/2008 9:47 37.51 17.8 8.6 10.7 799.2

12/15/2008 9:48 37.49 17.4 8.6 10.6 808.3

12/15/2008 9:49 37.28 17.1 8.7 10.6 809.4

12/15/2008 9:50 37.48 17.4 8.7 10.6 817.8

12/15/2008 9:51 37.9 17.4 8.7 10.6 814.3

12/15/2008 9:52 37.97 17.2 8.6 10.6 801.4

12/15/2008 9:53 38.28 17.3 8.6 10.7 800.1

12/15/2008 9:54 37.97 17.6 8.6 10.7 805.8

12/15/2008 9:55 38.11 17.6 8.6 10.6 803.6

12/15/2008 9:56 38.56 17.3 8.7 10.6 803.3

12/15/2008 9:57 38.36 17.6 8.7 10.7 814.3

12/15/2008 9:58 38.3 17.7 8.6 10.7 817.8

12/15/2008 9:59 38.6 17.7 8.7 10.6 809.6

12/15/2008 10:00 38.39 17.3 8.6 10.6 811.5

12/15/2008 10:01 38.23 17.4 8.7 10.6 814.1

12/15/2008 10:02 38.27 17.3 8.7 10.7 813.5

12/15/2008 10:03 38.55 17.5 8.7 10.6 808.8

12/15/2008 10:04 38.31 17.1 8.6 10.6 810

12/15/2008 10:05 38.82 17.1 8.7 10.6 803

12/15/2008 10:06 38.52 17.7 8.7 10.7 799

12/15/2008 10:07 38.34 17.6 8.7 10.6 817.4

12/15/2008 10:08 38.69 17 8.6 10.6 819.6

12/15/2008 10:09 38.43 16.8 8.7 10.6 816.2

12/15/2008 10:10 38.29 17 8.7 10.6 793.8

12/15/2008 10:11 38.18 17.2 8.7 10.6 788.2

12/15/2008 10:12 38.35 17.2 8.7 10.7 801.3

12/15/2008 10:13 38.46 17.7 8.7 10.7 808.5

12/15/2008 10:14 38.38 17.5 8.7 10.7 806.9

12/15/2008 10:15 38.6 17.5 8.7 10.7 806

12/15/2008 10:16 38.34 17.9 8.7 10.7 809.6

12/15/2008 10:17 38.52 18.4 8.7 10.7 813.1

12/15/2008 10:18 38.84 17.8 8.7 10.7 821.2

12/15/2008 10:19 38.72 17.8 8.7 10.7 810.2

12/15/2008 10:20 38.55 17.8 8.7 10.7 821.6

12/15/2008 10:21 38.67 18.3 8.7 10.7 810.8

12/15/2008 10:22 38.36 17.9 8.6 10.7 806.1

12/15/2008 10:23 38.79 18.1 8.7 10.7 805.4

12/15/2008 10:24 38.69 18.4 8.7 10.7 813.6

12/15/2008 10:25 38.51 18.2 8.7 10.7 816

Page 1 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 10:26 38.64 18.1 8.7 10.7 811.9

12/15/2008 10:27 38.41 18.1 8.7 10.7 808.9

12/15/2008 10:28 38.89 18.2 8.7 10.7 807.2

12/15/2008 10:29 38.83 17.9 8.7 10.7 812.3

12/15/2008 10:30 38.61 17.8 8.7 10.7 811.9

12/15/2008 10:31 38.52 18.3 8.7 10.7 819.2

12/15/2008 10:32 38.78 18.6 8.7 10.7 813.4

12/15/2008 10:33 38.69 18.2 8.7 10.7 809.8

12/15/2008 10:34 38.92 18.2 8.7 10.7 808.3

12/15/2008 10:35 38.71 18.2 8.7 10.7 804.3

12/15/2008 10:36 38.87 18.6 8.7 10.7 802.8

12/15/2008 10:37 38.89 18.4 8.7 10.7 809.7

12/15/2008 10:38 39.14 18.3 8.7 10.7 814.8

12/15/2008 10:39 39.08 18 8.7 10.7 819.1

12/15/2008 10:40 38.78 18.4 8.7 10.7 819.9

12/15/2008 10:41 38.63 18.4 8.7 10.8 820.7

12/15/2008 10:42 38.62 18.7 8.7 10.7 812.6

12/15/2008 10:43 38.63 18.9 8.7 10.7 808.1

12/15/2008 10:44 38.86 18.4 8.7 10.7 812.2

12/15/2008 10:45 38.72 18.5 8.7 10.7 804.3

12/15/2008 10:46 38.92 18.6 8.7 10.7 809.5

12/15/2008 10:47 38.87 18.9 8.7 10.7 819.4

12/15/2008 10:48 38.84 18.4 8.6 10.7 814.7

12/15/2008 10:49 38.97 18.2 8.7 10.7 807.5

12/15/2008 10:50 38.77 18.4 8.7 10.8 816.1

12/15/2008 10:51 38.82 18.8 8.7 10.7 814.4

12/15/2008 10:52 38.69 18.3 8.7 10.7 813.7

12/15/2008 10:53 38.49 18.4 8.7 10.7 814.1

12/15/2008 10:54 38.76 18.4 8.7 10.7 817

12/15/2008 10:55 38.51 18.1 8.7 10.8 815.1

12/15/2008 10:56 39.02 18.4 8.7 10.7 815.5

12/15/2008 10:57 39.03 18.1 8.7 10.7 817.7

12/15/2008 10:58 39.04 18.1 8.7 10.7 818

12/15/2008 10:59 39.06 17.7 8.7 10.7 816.7

12/15/2008 11:00 38.78 18 8.6 10.7 821.2

12/15/2008 11:01 38.97 18 8.6 10.7 822.8

12/15/2008 11:02 38.92 18.5 8.7 10.8 817.3

12/15/2008 11:03 38.91 18.7 8.7 10.7 815.8

12/15/2008 11:04 39.03 18.3 8.7 10.7 814

12/15/2008 11:05 39.19 18.3 8.7 10.7 808.1

Page 2 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 11:06 39.29 18.4 8.7 10.8 818.4

12/15/2008 11:07 39.01 18.8 8.6 10.8 820

12/15/2008 11:08 38.94 18.6 8.7 10.7 815.5

12/15/2008 11:09 38.92 18.2 8.7 10.7 811.2

12/15/2008 11:10 38.64 18.4 8.6 10.7 809.6

12/15/2008 11:11 38.5 18.5 8.7 10.8 811.7

12/15/2008 11:12 38.78 18.5 8.6 10.8 819.2

12/15/2008 11:13 38.87 18.3 8.6 10.8 815.6

12/15/2008 11:14 38.93 18.7 8.6 10.7 809.1

12/15/2008 11:15 39.22 18.6 8.6 10.7 809

12/15/2008 11:16 39.06 18.5 8.7 10.7 809.9

12/15/2008 11:17 38.81 18.7 8.7 10.8 811.8

12/15/2008 11:18 38.82 18.6 8.7 10.7 816.5

12/15/2008 11:19 38.51 18.3 8.6 10.7 806.2

12/15/2008 11:20 38.57 18.3 8.6 10.7 811.7

12/15/2008 11:21 38.56 18.4 8.6 10.7 818.4

12/15/2008 11:22 38.69 18.7 8.6 10.7 814.7

12/15/2008 11:23 38.78 18.1 8.7 10.7 802.2

12/15/2008 11:24 38.99 18.2 8.7 10.7 801.8

12/15/2008 11:25 38.93 18.4 8.7 10.7 808.6

12/15/2008 11:26 38.94 18.4 8.7 10.7 813.9

12/15/2008 11:27 39.09 18.2 8.7 10.7 803.9

12/15/2008 11:28 39.25 18.2 8.7 10.7 809.9

12/15/2008 11:29 39.27 17.6 8.7 10.7 818.5

12/15/2008 11:30 39.34 18 8.7 10.7 824.4

12/15/2008 11:31 39.5 18.4 8.7 10.7 826.5

12/15/2008 11:32 39.34 18.6 8.6 10.8 819.3

12/15/2008 11:33 39.4 18.6 8.6 10.8 820.2

12/15/2008 11:34 39.54 18.3 8.6 10.7 818.4

12/15/2008 11:35 39.68 18.6 8.6 10.8 818.7

12/15/2008 11:36 39.31 18.8 8.7 10.7 815

12/15/2008 11:37 38.86 18.5 8.6 10.8 817.2

12/15/2008 11:38 39.19 18.6 8.6 10.7 808.6

12/15/2008 11:39 39.03 18.1 8.6 10.7 813.4

12/15/2008 11:40 38.57 18.3 8.6 10.8 819.8

12/15/2008 11:41 38.52 18.4 8.6 10.8 818.2

12/15/2008 11:42 38.83 18.8 8.7 10.7 816.1

12/15/2008 11:43 38.82 18.9 8.7 10.8 819.5

12/15/2008 11:44 39.04 18.7 8.7 10.7 816.2

12/15/2008 11:45 39.2 18.4 8.7 10.7 810

Page 3 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 11:46 39.22 18.7 8.7 10.7 814.4

12/15/2008 11:47 39.04 19.1 8.7 10.7 815.1

12/15/2008 11:48 39.16 18.6 8.6 10.7 805.1

12/15/2008 11:49 39.37 18.1 8.6 10.7 808.7

12/15/2008 11:50 39.04 18.4 8.7 10.7 816

12/15/2008 11:51 39.27 18.8 8.6 10.8 819.6

12/15/2008 11:52 39 18.4 8.6 10.7 819.8

12/15/2008 11:53 39.13 18.3 8.7 10.7 814.6

12/15/2008 11:54 38.78 18.5 8.7 10.8 820.5

12/15/2008 11:55 38.64 18.7 8.6 10.8 822.3

12/15/2008 11:56 38.71 18.6 8.6 10.7 820.2

12/15/2008 11:57 38.99 18.4 8.7 10.7 815.8

12/15/2008 11:58 38.99 18.5 8.7 10.7 813.6

12/15/2008 11:59 38.98 18.3 8.6 10.7 814.6

12/15/2008 12:00 38.62 18.5 8.6 10.7 816.4

12/15/2008 12:01 39.12 18.3 8.7 10.7 814.9

12/15/2008 12:02 39.02 18.4 8.7 10.7 815.4

12/15/2008 12:03 39.2 18.6 8.7 10.8 817.5

12/15/2008 12:04 39.01 18.7 8.6 10.8 815.8

12/15/2008 12:05 39.19 18.6 8.6 10.7 814.5

12/15/2008 12:06 39.28 18.3 8.6 10.7 818.5

12/15/2008 12:07 39.04 18.4 8.6 10.8 810.8

12/15/2008 12:08 39.21 18.7 8.7 10.7 815

12/15/2008 12:09 39.11 18.7 8.7 10.7 814.5

12/15/2008 12:10 39.21 18.3 8.7 10.7 818.8

12/15/2008 12:11 39.51 18.4 8.7 10.8 820.6

12/15/2008 12:12 39.06 18.5 8.7 10.8 829.3

12/15/2008 12:13 39.25 18.7 8.7 10.7 819.5

12/15/2008 12:14 39.19 18.4 8.7 10.7 825.6

12/15/2008 12:15 39.48 18.3 8.7 10.7 814.7

12/15/2008 12:16 39.72 18.3 8.7 10.8 810.8

12/15/2008 12:17 39.18 18.8 8.7 10.7 813.2

12/15/2008 12:18 39.41 18.4 8.7 10.7 822.1

12/15/2008 12:19 39.17 17.8 8.7 10.7 826.2

12/15/2008 12:20 38.86 17.9 8.6 10.7 819.6

12/15/2008 12:21 39.44 18.4 8.7 10.8 814.7

12/15/2008 12:22 39.18 19 8.7 10.7 822.3

12/15/2008 12:23 39.14 18.5 8.6 10.7 808.5

12/15/2008 12:24 39.27 18.4 8.6 10.8 817.4

12/15/2008 12:25 39.54 18.6 8.7 10.8 820.9

Page 4 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 12:26 35.61 14.1 4.9 10.8 813.9

12/15/2008 12:27 2.84 0.1 0.6 10.7 817.2

12/15/2008 12:28 19.31 11.4 7.6 10.7 821.4

12/15/2008 12:29 37.84 17.6 8.6 10.7 822.9

12/15/2008 12:30 39.07 18.4 8.6 10.7 813

12/15/2008 12:31 39.04 18.6 8.6 10.8 813.6

12/15/2008 12:32 38.81 18.8 8.6 10.8 824.8

12/15/2008 12:33 39.17 18.9 8.6 10.7 817.7

12/15/2008 12:34 39.19 18.6 8.6 10.7 823.5

12/15/2008 12:35 38.91 18.6 8.6 10.7 821

12/15/2008 12:36 38.73 18.7 8.6 10.8 823.1

12/15/2008 12:37 38.95 18.8 8.6 10.7 817.6

12/15/2008 12:38 38.99 18.4 8.6 10.7 813.6

12/15/2008 12:39 39.05 18 8.6 10.7 807.3

12/15/2008 12:40 39.04 17.9 8.6 10.7 813.5

12/15/2008 12:41 39.19 18.1 8.6 10.7 813.7

12/15/2008 12:42 38.9 18 8.6 10.7 803.6

12/15/2008 12:43 38.86 18 8.6 10.7 806.3

12/15/2008 12:44 38.99 18 8.6 10.7 815.6

12/15/2008 12:45 38.87 18.2 8.6 10.7 813.9

12/15/2008 12:46 38.92 18.1 8.6 10.7 820

12/15/2008 12:47 38.97 17.6 8.6 10.7 821.8

12/15/2008 12:48 39.49 17.6 8.6 10.6 825.9

12/15/2008 12:49 39.44 17.2 8.6 10.7 810

12/15/2008 12:50 39.37 17.9 8.6 10.7 818.6

12/15/2008 12:51 39.61 18.1 8.6 10.7 820

12/15/2008 12:52 39.73 18.1 8.6 10.7 820.8

12/15/2008 12:53 39.42 18.4 8.6 10.7 817.1

12/15/2008 12:54 39.81 18.3 8.6 10.7 810.2

12/15/2008 12:55 39.28 18.6 8.6 10.7 810.2

12/15/2008 12:56 39.22 18.4 8.6 10.7 813.7

12/15/2008 12:57 39.59 18.2 8.6 10.7 811

12/15/2008 12:58 39.6 18.3 8.6 10.7 814.6

12/15/2008 12:59 39.76 18.5 8.6 10.7 817.4

12/15/2008 13:00 39.38 18.4 8.6 10.7 820.4

12/15/2008 13:01 39.42 18.2 8.6 10.7 818.8

12/15/2008 13:02 39.85 18.3 8.6 10.7 820.7

12/15/2008 13:03 39.99 18.3 8.6 10.7 820.7

12/15/2008 13:04 39.73 18.3 8.6 10.7 810.9

12/15/2008 13:05 39.96 18.6 8.6 10.7 813.1

Page 5 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 13:06 39.45 18.4 8.6 10.7 811.8

12/15/2008 13:07 39.69 18.2 8.6 10.7 813.6

12/15/2008 13:08 39.83 18.4 8.6 10.7 813.9

12/15/2008 13:09 39.64 18.5 8.6 10.7 821.5

12/15/2008 13:10 39.36 18.1 8.6 10.7 826.1

12/15/2008 13:11 39.02 18.4 8.6 10.7 819.7

12/15/2008 13:12 38.83 18.6 8.6 10.7 818.4

12/15/2008 13:13 38.74 18.6 8.6 10.7 821.5

12/15/2008 13:14 38.4 18.6 8.6 10.7 809.2

12/15/2008 13:15 38.73 18.3 8.6 10.7 824

12/15/2008 13:16 38.71 18.3 8.6 10.7 799.4

12/15/2008 13:17 38.53 18.5 8.6 10.8 804.3

12/15/2008 13:18 38.42 18.8 8.6 10.7 817.6

12/15/2008 13:19 38.42 18 8.6 10.7 817.4

12/15/2008 13:20 38.2 18.3 8.6 10.7 828.3

12/15/2008 13:21 37.85 18.7 8.6 10.7 825.6

12/15/2008 13:22 37.95 18.8 8.6 10.7 823.5

12/15/2008 13:23 37.7 18.6 8.6 10.7 813.4

12/15/2008 13:24 38.06 18.6 8.6 10.7 822.5

12/15/2008 13:25 38.15 18.7 8.6 10.7 819.5

12/15/2008 13:26 38.49 18.9 8.6 10.7 820.4

12/15/2008 13:27 38.74 18.8 8.6 10.7 831.1

12/15/2008 13:28 39.02 18.6 8.6 10.7 808

12/15/2008 13:29 38.87 18.4 8.6 10.7 809

12/15/2008 13:30 38.98 18.7 8.6 10.7 818.9

12/15/2008 13:31 39.29 18.8 8.6 10.7 824.5

12/15/2008 13:32 39.29 18.5 8.6 10.7 817.4

12/15/2008 13:33 39.5 18.6 8.6 10.8 813.9

12/15/2008 13:34 39.39 18.9 8.6 10.8 813

12/15/2008 13:35 39.2 18.6 8.6 10.7 815.8

12/15/2008 13:36 39.56 18.4 8.6 10.7 827.1

12/15/2008 13:37 39.73 18.7 8.6 10.8 821.7

12/15/2008 13:38 39.65 18.6 8.6 10.7 817.1

12/15/2008 13:39 39.27 18 8.6 10.7 820.1

12/15/2008 13:40 39.35 18.1 8.6 10.7 810.7

12/15/2008 13:41 39.15 18.4 8.6 10.7 815.2

12/15/2008 13:42 39.15 18.8 8.6 10.8 815.1

12/15/2008 13:43 39.47 18.6 8.6 10.7 814.7

12/15/2008 13:44 39.65 18.4 8.6 10.7 804.5

12/15/2008 13:45 39.77 18.4 8.6 10.7 811.3

Page 6 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 13:46 39.66 18.5 8.6 10.8 816.3

12/15/2008 13:47 39.87 18.8 8.6 10.8 804.6

12/15/2008 13:48 39.63 18.6 8.6 10.7 793.3

12/15/2008 13:49 39.46 18.1 8.6 10.7 806.9

12/15/2008 13:50 38.94 18.5 8.6 10.8 819.5

12/15/2008 13:51 38.67 18.7 8.6 10.7 814

12/15/2008 13:52 39.55 18.8 8.6 10.8 816

12/15/2008 13:53 38.91 19 8.6 10.7 818.8

12/15/2008 13:54 39.31 18.7 8.6 10.8 821.2

12/15/2008 13:55 39.34 18.7 8.6 10.7 823.7

12/15/2008 13:56 39.43 18.7 8.6 10.7 815

12/15/2008 13:57 38.85 18.9 8.6 10.8 824.6

12/15/2008 13:58 38.94 18.8 8.6 10.7 812.9

12/15/2008 13:59 39.19 18 8.6 10.7 816.5

12/15/2008 14:00 39.2 17.9 8.6 10.7 802.7

12/15/2008 14:01 39.16 18.2 8.6 10.7 812.6

12/15/2008 14:02 39.23 18.6 8.6 10.7 815.5

12/15/2008 14:03 39.41 18.1 8.6 10.7 824.4

12/15/2008 14:04 39.56 18.2 8.6 10.7 834.1

12/15/2008 14:05 39.54 18.2 8.6 10.7 833.3

12/15/2008 14:06 39.69 18.1 8.6 10.8 813.2

12/15/2008 14:07 39.72 18.4 8.6 10.8 825.5

12/15/2008 14:08 39.69 18.6 8.6 10.7 814.3

12/15/2008 14:09 39.4 17.7 8.6 10.7 825.2

12/15/2008 14:10 39.01 18 8.6 10.7 813.4

12/15/2008 14:11 39.18 18.5 8.6 10.8 818

12/15/2008 14:12 39.3 18.8 8.6 10.8 818.2

12/15/2008 14:13 39.37 18.7 8.6 10.7 813.7

12/15/2008 14:14 39.83 18.6 8.6 10.7 826.4

12/15/2008 14:15 39.81 18.7 8.6 10.8 810.7

12/15/2008 14:16 39.84 18.7 8.6 10.8 817.5

12/15/2008 14:17 39.5 19 8.6 10.8 816.1

12/15/2008 14:18 39.54 18.7 8.6 10.7 824.4

12/15/2008 14:19 39.82 18.4 8.6 10.7 806.5

12/15/2008 14:20 39.32 18.4 8.6 10.8 818.4

12/15/2008 14:21 39.49 18.5 8.6 10.8 819.2

12/15/2008 14:22 39.66 18.7 8.6 10.8 821.6

12/15/2008 14:23 39.62 19.2 8.6 10.8 819.5

12/15/2008 14:24 39.42 18.9 8.6 10.8 813.8

12/15/2008 14:25 39.02 18.8 8.6 10.8 818.2

Page 7 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 14:26 39.01 19 8.6 10.8 806.3

12/15/2008 14:27 39.07 19 8.6 10.7 822

12/15/2008 14:28 38.7 18.8 8.6 10.7 820.4

12/15/2008 14:29 38.68 18.7 8.6 10.8 823

12/15/2008 14:30 38.65 18.9 8.6 10.8 827

12/15/2008 14:31 38.89 18.8 8.6 10.8 820.4

Averages: 38.770 18.21 8.59 10.71 814.92

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 9:05 40.68 18.2 8.7 2.8 796.6

12/16/2008 9:06 40.64 18.4 8.7 8.2 805.6

12/16/2008 9:07 40.75 18.6 8.7 10.9 811.4

12/16/2008 9:08 40.4 18.2 8.7 10.9 809.6

12/16/2008 9:09 40.11 18.1 8.7 10.9 807

12/16/2008 9:10 40.25 18.1 8.7 10.9 807.3

12/16/2008 9:11 40.33 18.2 8.7 10.9 809.7

12/16/2008 9:12 39.98 17.8 8.6 10.9 810.6

12/16/2008 9:13 40.26 18.1 8.6 10.9 814.2

12/16/2008 9:14 40.28 18.4 8.6 10.9 813.1

12/16/2008 9:15 40.38 18.2 8.6 10.9 812.5

12/16/2008 9:16 40.15 17.9 8.6 10.9 815.3

12/16/2008 9:17 40.34 18.1 8.6 10.9 817.4

12/16/2008 9:18 40.44 18.1 8.6 10.9 816.8

12/16/2008 9:19 40.55 18.2 8.6 10.9 811.2

12/16/2008 9:20 40.65 17.8 8.6 10.9 812

12/16/2008 9:21 40.29 17.8 8.5 10.9 809.8

12/16/2008 9:22 40.32 18.2 8.5 10.9 805.7

12/16/2008 9:23 40.3 18.3 8.5 10.9 800.9

12/16/2008 9:24 40.2 18 8.5 10.9 805.1

12/16/2008 9:25 40.15 17.8 8.5 10.9 804.2

12/16/2008 9:26 40.32 17.7 8.5 10.9 807.5

12/16/2008 9:27 40.21 17.7 8.5 10.9 803.3

12/16/2008 9:28 40.46 18.2 8.5 10.9 808.5

12/16/2008 9:29 40.59 17.7 8.5 10.9 812.1

12/16/2008 9:30 40.15 17.3 8.5 10.9 811.5

12/16/2008 9:31 39.89 17.5 8.5 10.9 811.5

12/16/2008 9:32 40.4 17.9 8.5 10.9 800

12/16/2008 9:33 40.74 18.1 8.5 10.9 800.1

12/16/2008 9:34 41.04 17.8 8.5 10.9 803.1

12/16/2008 9:35 40.72 17.9 8.5 10.9 816.6

Page 8 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 9:36 40.64 18 8.5 10.9 807.9

12/16/2008 9:37 40.43 18.2 8.5 10.9 808.6

12/16/2008 9:38 40.75 18 8.5 10.8 805.7

12/16/2008 9:39 40.53 17.6 8.5 10.8 807.8

12/16/2008 9:40 40.47 16.9 8.5 10.8 805.5

12/16/2008 9:41 40.28 17.1 8.5 10.8 805.5

12/16/2008 9:42 40.58 17.6 8.5 10.8 797.6

12/16/2008 9:43 40.59 17.9 8.5 10.8 810.4

12/16/2008 9:44 40.72 17.5 8.5 10.8 806.1

12/16/2008 9:45 40.52 17.3 8.5 10.8 812.8

12/16/2008 9:46 40.95 17.5 8.5 10.8 811.2

12/16/2008 9:47 41.38 17.3 8.5 10.9 807.4

12/16/2008 9:48 41.17 17.6 8.5 10.9 803.6

12/16/2008 9:49 41.11 17.5 8.5 10.8 812.8

12/16/2008 9:50 40.92 17.2 8.5 10.8 816

12/16/2008 9:51 40.75 17.5 8.5 10.9 811.2

12/16/2008 9:52 40.95 17.9 8.5 10.9 810.7

12/16/2008 9:53 41.31 17.9 8.5 10.9 804.8

12/16/2008 9:54 40.65 17.7 8.5 10.9 802.6

12/16/2008 9:55 40.54 17.6 8.5 10.9 802.1

12/16/2008 9:56 40.62 17.6 8.5 10.9 810.6

12/16/2008 9:57 40.3 17.8 8.5 10.9 817.6

12/16/2008 9:58 40.19 17.9 8.5 10.8 814.8

12/16/2008 9:59 40.17 17.7 8.5 10.9 813.7

12/16/2008 10:00 40.19 17.7 8.5 10.9 808.8

12/16/2008 10:01 40.7 17.6 8.5 10.9 813

12/16/2008 10:02 40.66 17.7 8.6 10.8 805.1

12/16/2008 10:03 40.96 17.9 8.6 10.9 804.4

12/16/2008 10:04 40.77 17.9 8.5 10.9 813.8

12/16/2008 10:05 40.67 17.6 8.5 10.9 813.6

12/16/2008 10:06 41.25 17.7 8.6 10.9 816.6

12/16/2008 10:07 41.2 17.8 8.5 10.9 819.1

12/16/2008 10:08 41.49 17.9 8.5 10.8 815.4

12/16/2008 10:09 41.6 17.4 8.6 10.8 813.5

12/16/2008 10:10 41.11 17.2 8.6 10.8 814.6

12/16/2008 10:11 40.72 17.4 8.5 10.8 814.7

12/16/2008 10:12 40.92 17.7 8.5 10.9 817.8

12/16/2008 10:13 40.7 17.8 8.5 10.9 818.1

12/16/2008 10:14 40.61 17.7 8.5 10.9 814.4

12/16/2008 10:15 40.72 17.8 8.5 10.9 823.3

Page 9 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 10:16 40.42 17.5 8.5 10.9 814.6

12/16/2008 10:17 40.64 17.7 8.5 10.9 816.1

12/16/2008 10:18 40.47 17.9 8.5 10.9 814.5

12/16/2008 10:19 40.21 17.7 8.4 10.8 810.4

12/16/2008 10:20 40.06 17.5 8.4 10.9 806.4

12/16/2008 10:21 39.69 17.4 8.4 10.9 812.7

12/16/2008 10:22 39.65 17.6 8.4 10.9 809.3

12/16/2008 10:23 39.76 17.9 8.4 10.9 806.7

12/16/2008 10:24 39.67 17.9 8.4 10.9 809.9

12/16/2008 10:25 39.39 17.7 8.4 10.9 813.7

12/16/2008 10:26 39.69 17.7 8.3 10.9 807.8

12/16/2008 10:27 39.36 17.9 8.4 10.9 804.6

12/16/2008 10:28 39.81 18.1 8.4 10.9 811.6

12/16/2008 10:29 39.86 17.7 8.4 10.9 813.9

12/16/2008 10:30 39.62 17.2 8.3 10.9 809.5

12/16/2008 10:31 39.06 17.7 8.3 10.9 817.3

12/16/2008 10:32 39.03 17.9 8.3 10.9 819.4

12/16/2008 10:33 38.89 17.8 8.3 10.9 814.5

12/16/2008 10:34 39.02 17.7 8.3 10.9 817.8

12/16/2008 10:35 38.91 17.8 8.3 10.9 817.9

12/16/2008 10:36 39.05 18 8.3 10.9 827.4

12/16/2008 10:37 39.34 18 8.3 10.9 821.5

12/16/2008 10:38 39.4 17.7 8.3 10.9 810.9

12/16/2008 10:39 38.85 17.7 8.3 10.9 799.9

12/16/2008 10:40 39.08 17.5 8.3 10.9 807.3

12/16/2008 10:41 39.34 17.8 8.3 10.9 809.4

12/16/2008 10:42 39.6 17.9 8.3 10.9 819.8

12/16/2008 10:43 39.41 17.8 8.3 10.9 811

12/16/2008 10:44 39.44 17.8 8.3 10.9 805.4

12/16/2008 10:45 39.5 17.7 8.3 10.9 811.2

12/16/2008 10:46 39.72 17.7 8.3 10.9 814

12/16/2008 10:47 39.51 18.1 8.4 10.9 815

12/16/2008 10:48 39.32 18.1 8.4 10.9 818

12/16/2008 10:49 39.36 17.8 8.4 10.9 816.2

12/16/2008 10:50 39.37 17.8 8.4 10.9 825.9

12/16/2008 10:51 39.19 17.8 8.4 10.9 818.2

12/16/2008 10:52 39.45 17.8 8.4 10.9 815.9

12/16/2008 10:53 39.41 17.9 8.4 10.9 811.9

12/16/2008 10:54 39.39 17.9 8.4 10.9 813.2

12/16/2008 10:55 39.55 17.9 8.4 10.9 812.6

Page 10 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 10:56 39.35 17.8 8.4 10.8 807.9

12/16/2008 10:57 39.46 17.7 8.4 10.9 807

12/16/2008 10:58 38.94 17.6 8.4 10.8 809.8

12/16/2008 10:59 39.23 17.3 8.4 10.8 811.5

12/16/2008 11:00 38.97 16.7 8.4 10.8 803.8

12/16/2008 11:01 39.15 17 8.4 10.8 804.1

12/16/2008 11:02 38.97 17.2 8.4 10.8 816.9

12/16/2008 11:03 39.26 17.5 8.5 10.8 815

12/16/2008 11:04 39.83 17.4 8.5 10.8 820.3

12/16/2008 11:05 39.58 17.2 8.5 10.8 819.9

12/16/2008 11:06 39.69 17 8.5 10.8 812.5

12/16/2008 11:07 39.81 17.2 8.5 10.8 803.9

12/16/2008 11:08 39.89 17.4 8.5 10.9 808

12/16/2008 11:09 39.88 17.3 8.5 10.8 817

12/16/2008 11:10 39.39 17.5 8.5 10.8 822.3

12/16/2008 11:11 39.02 17.4 8.5 10.9 817.6

12/16/2008 11:12 39.41 17.5 8.5 10.9 810.6

12/16/2008 11:13 39.51 17.6 8.5 10.8 817

12/16/2008 11:14 39.26 17.5 8.5 10.9 813.8

12/16/2008 11:15 39.42 17.5 8.5 10.9 810.6

12/16/2008 11:16 39.24 17.8 8.5 10.9 808.5

12/16/2008 11:17 39.13 17.9 8.5 10.8 819.5

12/16/2008 11:18 39.7 17.8 8.6 10.9 816.3

12/16/2008 11:19 39.48 17.4 8.5 10.8 811.1

12/16/2008 11:20 39.74 17.3 8.6 10.8 811.2

12/16/2008 11:21 39.57 17.5 8.6 10.8 809.4

12/16/2008 11:22 39.61 17.7 8.6 10.9 801.4

12/16/2008 11:23 39.64 17.5 8.6 10.9 802.8

12/16/2008 11:24 39.54 17.6 8.6 10.9 794.3

12/16/2008 11:25 39.19 17.9 8.6 10.8 805.5

12/16/2008 11:26 39.27 17.7 8.6 10.8 810.3

12/16/2008 11:27 39.18 17.6 8.6 10.9 815.7

12/16/2008 11:28 39.29 17.6 8.6 10.9 805.1

12/16/2008 11:29 39.44 17.4 8.6 10.8 810.2

12/16/2008 11:30 39.09 16.8 8.6 10.8 812.3

12/16/2008 11:31 39.19 17.5 8.6 10.9 815.8

12/16/2008 11:32 39.24 17.4 8.6 10.9 817

12/16/2008 11:33 39.28 17.5 8.6 10.9 817.5

12/16/2008 11:34 39.42 17.7 8.6 10.9 816.3

12/16/2008 11:35 39.67 17.7 8.6 10.9 809.7

Page 11 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 11:36 39.54 17.6 8.6 10.9 815.3

12/16/2008 11:37 39.55 17.7 8.6 10.9 811.5

12/16/2008 11:38 39.52 18.1 8.6 10.9 807.3

12/16/2008 11:39 39.67 18 8.6 10.9 815.8

12/16/2008 11:40 39.59 17.4 8.6 10.9 818.6

12/16/2008 11:41 39.36 17.5 8.6 10.9 821.5

12/16/2008 11:42 39.48 17.8 8.6 10.9 807.1

12/16/2008 11:43 39.15 17.8 8.6 10.9 820.8

12/16/2008 11:44 39.39 17.9 8.6 10.9 812.6

12/16/2008 11:45 39.12 17.9 8.7 10.9 818

12/16/2008 11:46 39.14 17.9 8.7 10.9 820.8

12/16/2008 11:47 39.54 17.8 8.7 10.9 812.4

12/16/2008 11:48 39.34 18.2 8.7 10.9 812.8

12/16/2008 11:49 39.67 17.8 8.7 10.9 815.6

12/16/2008 11:50 39.82 17.8 8.7 10.9 815.6

12/16/2008 11:51 39.5 17.9 8.7 10.9 812.1

12/16/2008 11:52 39.33 18 8.7 10.9 812.6

12/16/2008 11:53 39.25 18 8.7 10.9 814.7

12/16/2008 11:54 39.23 18.4 8.7 10.9 812.3

12/16/2008 11:55 39.17 18.5 8.7 10.9 815.6

12/16/2008 11:56 39.11 18.1 8.7 10.9 809.9

12/16/2008 11:57 39.39 18.2 8.7 10.9 821.5

12/16/2008 11:58 39.31 18.3 8.7 10.9 808.7

12/16/2008 11:59 39.51 18.1 8.7 10.9 818.1

12/16/2008 12:00 39.25 18 8.7 10.9 810.8

12/16/2008 12:01 39.32 18.1 8.7 10.9 809.1

12/16/2008 12:02 39.26 18.6 8.7 10.9 820.2

12/16/2008 12:03 39.14 18.2 8.7 10.9 820.6

12/16/2008 12:04 39.28 18.1 8.7 10.9 815.7

12/16/2008 12:05 39.25 18.1 8.7 10.9 811.4

12/16/2008 12:06 39.32 18.3 8.7 10.9 820

12/16/2008 12:07 39.19 18.2 8.7 10.9 821.4

12/16/2008 12:08 39.38 18.3 8.7 11 822.6

12/16/2008 12:09 39.21 18.3 8.7 10.9 824

12/16/2008 12:10 39.15 18 8.7 10.9 818.6

12/16/2008 12:11 38.94 17.9 8.7 10.9 816.4

12/16/2008 12:12 39.07 18.1 8.7 11 815.9

12/16/2008 12:13 39.03 18.5 8.7 11 824.5

12/16/2008 12:14 39.25 18.4 8.7 10.9 826.7

12/16/2008 12:15 39.47 17.9 8.7 10.9 820.7

Page 12 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 12:16 39.19 17.9 8.7 10.9 814.6

12/16/2008 12:17 39.34 18 8.7 10.9 829.6

12/16/2008 12:18 39.13 17.8 8.7 10.9 816.6

12/16/2008 12:19 39.51 17.6 8.7 10.9 810.9

12/16/2008 12:20 39.3 17.2 8.7 10.9 811.8

12/16/2008 12:21 38.9 17.4 8.7 10.9 805.9

12/16/2008 12:22 39.24 17.7 8.7 10.9 806.3

12/16/2008 12:23 39.26 17.9 8.7 10.9 818.2

12/16/2008 12:24 39.68 18.1 8.7 10.9 812.2

12/16/2008 12:25 39.84 17.7 8.7 10.9 809.2

12/16/2008 12:26 33.7 12 4.9 10.9 814.6

12/16/2008 12:27 3.16 0.1 0.6 10.9 819.9

12/16/2008 12:28 20.92 11.2 7.5 11 812.1

12/16/2008 12:29 38.56 17.5 8.6 10.9 816.8

12/16/2008 12:30 39.05 17.8 8.6 10.9 818.9

12/16/2008 12:31 38.93 18.1 8.6 10.9 819.4

12/16/2008 12:32 38.94 18.1 8.6 10.9 820.1

12/16/2008 12:33 39.14 18.2 8.6 11 827.2

12/16/2008 12:34 39.46 18.5 8.6 11 824.5

12/16/2008 12:35 38.84 18.3 8.6 11 813.5

12/16/2008 12:36 39 18.5 8.6 11 815.7

12/16/2008 12:37 39.11 18.3 8.6 11 808.6

12/16/2008 12:38 38.62 18.3 8.6 11 825.2

12/16/2008 12:39 38.94 18.7 8.6 11 821.6

12/16/2008 12:40 38.6 18.3 8.6 10.9 818.2

12/16/2008 12:41 38.88 18.2 8.6 11 815

12/16/2008 12:42 38.8 18.1 8.6 11 819.2

12/16/2008 12:43 38.72 18.5 8.6 11 814.5

12/16/2008 12:44 38.63 18.5 8.6 11 813.3

12/16/2008 12:45 38.62 18.5 8.7 11 814.8

12/16/2008 12:46 39.04 18.4 8.6 11 811.8

12/16/2008 12:47 38.73 18.2 8.6 10.9 809.1

12/16/2008 12:48 39.01 18.1 8.6 11 809.4

12/16/2008 12:49 39.08 18.2 8.6 10.9 820.8

12/16/2008 12:50 39.38 17.7 8.7 10.9 814.9

12/16/2008 12:51 39.51 17.9 8.7 11 815.5

12/16/2008 12:52 39.24 18.1 8.6 11 820.6

12/16/2008 12:53 39.11 18.2 8.7 11 821.9

12/16/2008 12:54 39.52 18.6 8.7 11 820

12/16/2008 12:55 39.46 18.6 8.7 11 814.6

Page 13 of 14
SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 12:56 39.17 18.4 8.7 10.9 801.9

12/16/2008 12:57 39.38 18.5 8.7 10.9 806.5

12/16/2008 12:58 39.27 18.6 8.7 11 818.4

12/16/2008 12:59 38.97 18.8 8.7 11 817.5

12/16/2008 13:00 39.08 18.4 8.7 10.9 826.8

12/16/2008 13:01 39.28 18.2 8.7 11 819.2

12/16/2008 13:02 38.88 18.4 8.7 11 811.1

12/16/2008 13:03 39.03 18.9 8.7 11 823.4

12/16/2008 13:04 38.98 18.8 8.7 11 821.7

12/16/2008 13:05 38.93 18.4 8.7 11 813.1

12/16/2008 13:06 39.13 18.3 8.7 11 811.5

12/16/2008 13:07 38.75 18.6 8.7 11 813.1

12/16/2008 13:08 39.07 18.8 8.7 11 812.9

12/16/2008 13:09 39.47 18.7 8.7 11 816.7

12/16/2008 13:10 39.24 18.3 8.7 11 819.6

12/16/2008 13:11 38.92 18.4 8.7 11 818.3

12/16/2008 13:12 39.1 18.4 8.7 11 816.4

12/16/2008 13:13 39.48 18.7 8.7 11 812.1

12/16/2008 13:14 39.28 18.9 8.7 11 818.7

12/16/2008 13:15 39.15 18.3 8.7 11 813.1

12/16/2008 13:16 39.23 18.4 8.7 11 823.5

12/16/2008 13:17 39.21 18.5 8.7 11 812

12/16/2008 13:18 39.47 18.6 8.7 11 819.5

12/16/2008 13:19 39.21 19 8.7 10.9 824.3

12/16/2008 13:20 39.13 18.3 8.7 11 807.8

Averages 39.435 17.78 8.512 10.86 813.25

Page 14 of 14
APPENDIX G 

VISIBLE EMISSIONS DATA SHEET 

APPENDIX H 

TEST PARTICIPANTS 
TEST PARTICIPANTS

AIR SERVICES GROUP 

TEST TEAM

Jorge Varino Environmental Technician – Team Lead 

Gary Barber Environmental Technician 

Scott Given Environmental Technician 

Ryan Newell Associate Technician 

David A. Smith Coordinator, Air Services Group 

PROCESS DATA

Raymond A. McDarby Senior Environmental Technician 

FUEL ANALYSIS

John McDaniel Senior Engineering Fellow– Polk Power Station 

REPORT PREPARATION

Raymond A. McDarby Senior Environmental Technician 

QUALITY ASSURANCE / QUALITY CONTROL

Raymond A. McDarby Senior Environmental Technician 

POLK POWER STATION

Michael Perkins Environmental Coordinator 

Joshua Ellwein Principal Engineer