13339 Hagers Ferry Road

Huntersville, NC 28078-7929

McGuire Nuclear Complex - MG03A2

Phone: 980-875-5245 Fax: 980-875-4349

Order Summary Report

Analytical Laboratory

Order Number: J11090012

Lab Contact: Jason C Perkins

Date: 9/28/2011

Customer Address: 3195 Pine Hall Rd

Customer Name(s): Bill Kennedy, Melonie Martin, Wayne Chapman, Tom Johnson

Mailcode: Belews Steam Station

Belews Creek, NC 28012

Phone: 980-875-5348

Report Authorized By:

(Signature)

Program Comments:

Please contact the Program Manager (Jason C Perkins) with any questions regarding this report.

Data Flags & Calculations:

Any analytical tests or individual analytes within a test flagged with a Qualifier indicate a deviation from the method quality

system or quality control requirement. The qualifier description is found at the end of the Certificate of Analysis (sample results) 

under the qualifiers heading. All results are reported on a dry weight basis unless otherwise noted.

Data Package:

This data package includes analytical results that are applicable only to the samples described in this narrative. An estimation of 

the uncertainty of measurement for the results in the report is available upon request. This report shall not be reproduced, except 

in full, without the written consent of the Analytical Laboratory. Please contact the Analytical laboratory with any questions. The 

order of individual sections within this report is as follows:

Job Summary Report, Sample Identification, Technical Validation of Data Package, Analytical Laboratory Certificate of Analysis,

Analytical Laboratory QC Reports, Sub-contracted Laboratory Results, Customer Specific Data Sheets, Reports & 

Documentation, Customer Database Entries, Test Case Narratives, Chain of Custody (COC)

Certification:

The Analytical Laboratory holds the following State Certifications : North Carolina (DENR) Certificate #248, South Carolina 

(DHEC) Laboratory ID # 99005. Contact the Analytical Laboratory for definitive information about the certification status of 

specific methods. 

Analytical Lab 

Page 1 of 27
Sample ID's & Descriptions:

Sample ID Plant/Station

Collection 

Date and Time Collected By Sample Description

2011019120 BELEWS 14-Sep-11 7:30 AM W. B. WORKMAN FGD Purge Eff 

2011019121 BELEWS 14-Sep-11 7:35 AM W. B. WORKMAN EQ TANK EFF. 

2011019122 BELEWS 14-Sep-11 7:40 AM W. B. WORKMAN BIOREACTOR 1 INF. 

2011019123 BELEWS 14-Sep-11 7:45 AM W. B. WORKMAN BIOREACTOR 2 INF. 

2011019124 BELEWS 14-Sep-11 7:50 AM W. B. WORKMAN BIOREACTOR 2 EFF. 

2011019125 BELEWS 14-Sep-11 8:00 AM W. B. WORKMAN FILTER BLANK 

2011019126 BELEWS 01-Sep-11 10:30 AM A. Moose Trip Blank 

2011019127 BELEWS 14-Sep-11 12:55 PM DAVID MORRIS BIOREACTOR 1 INF. 

2011019128 BELEWS 14-Sep-11 12:55 PM DAVID MORRIS HG BLANK BIOREACTOR 1 INF. 

2011019129 BELEWS 14-Sep-11 1:15 PM DAVID MORRIS BIOREACTOR 2 INF. 

2011019130 BELEWS 14-Sep-11 1:15 PM DAVID MORRIS Hg Blk BioReactor 2 Inf 

2011019131 BELEWS 14-Sep-11 1:00 PM DAVID MORRIS BIOREACTOR 2 EFF. 

2011019132 BELEWS 14-Sep-11 1:00 PM DAVID MORRIS Hg Blk BioReactor 2 Eff 

13 Total Samples

Analytical Lab 

Page 2 of 27
COC and .pdf report are in agreement with sample totals 

and analyses (compliance programs and procedures).

All Results are less than the laboratory reporting limits.

All laboratory QA/QC requirements are acceptable.

The Vendor Laboratories have been qualified by the 

Analytical Laboratory

Yes No

Technical Validation Review

Checklist:

Yes No

Yes No

Report Sections Included:

Job Summary Report Sub-contracted Laboratory Results

Sample Identification Customer Specific Data Sheets, Reports, & Documentation

Technical Validation of Data Package Customer Database Entries

Analytical Laboratory Certificate of Analysis

Analytical Laboratory QC Report

Chain of Custody

Reviewed By: Mary Ann Ogle Date: 9/28/2011

Yes

Electronic Data Deliverable (EDD) Sent Separately

Analytical Lab 

Page 3 of 27
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11090012

2011019120

Collection Date: 14-Sep-11 7:30 AM

Site: FGD Purge Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

INORGANIC IONS BY IC

Bromide 84 mg/L EPA 300.0 22-Sep-11 20:11 CLEEMAN 10

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) 239 ug/L EPA 245.1 16-Sep-11 09:05 AGIBBS 5

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 141 mg/L EPA 200.7 16-Sep-11 10:28 DJSULL1 0.5

DISSOLVED METALS BY ICP-MS

Selenium (Se) 1120 ug/L EPA 200.8 15-Sep-11 13:38 KRICHAR 10

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) 264 ug/L EPA 200.8 19-Sep-11 10:24 DJSULL1 10

Chromium (Cr) 262 ug/L EPA 200.8 19-Sep-11 10:24 DJSULL1 10

Copper (Cu) 185 ug/L EPA 200.8 19-Sep-11 10:24 DJSULL1 10

Nickel (Ni) 237 ug/L EPA 200.8 19-Sep-11 10:24 DJSULL1 10

Selenium (Se) 6110 ug/L EPA 200.8 19-Sep-11 10:24 DJSULL1 20

Silver (Ag) < 10 ug/L EPA 200.8 19-Sep-11 10:24 DJSULL1 10

Zinc (Zn) 317 ug/L EPA 200.8 19-Sep-11 10:24 DJSULL1 20

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

TOTAL DISSOLVED SOLIDS

TDS 15000 mg/L SM2540C 19-Sep-11 15:00 TJA7067 200

2011019121

Collection Date: 14-Sep-11 7:35 AM

Site: EQ TANK EFF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) 189 ug/L EPA 245.1 16-Sep-11 09:07 AGIBBS 2.5

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 156 mg/L EPA 200.7 16-Sep-11 10:32 DJSULL1 0.5

DISSOLVED METALS BY ICP-MS

Selenium (Se) 628 ug/L EPA 200.8 15-Sep-11 13:41 KRICHAR 10

Analytical Lab 

Page 4 of 27
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11090012

2011019121

Collection Date: 14-Sep-11 7:35 AM

Site: EQ TANK EFF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) 222 ug/L EPA 200.8 19-Sep-11 10:27 DJSULL1 10

Chromium (Cr) 240 ug/L EPA 200.8 19-Sep-11 10:27 DJSULL1 10

Copper (Cu) 167 ug/L EPA 200.8 19-Sep-11 10:27 DJSULL1 10

Nickel (Ni) 225 ug/L EPA 200.8 19-Sep-11 10:27 DJSULL1 10

Selenium (Se) 5250 ug/L EPA 200.8 19-Sep-11 10:27 DJSULL1 20

Silver (Ag) < 10 ug/L EPA 200.8 19-Sep-11 10:27 DJSULL1 10

Zinc (Zn) 291 ug/L EPA 200.8 19-Sep-11 10:27 DJSULL1 20

2011019122

Collection Date: 14-Sep-11 7:40 AM

Site: BIOREACTOR 1 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 149 mg/L EPA 200.7 16-Sep-11 10:36 DJSULL1 0.5

DISSOLVED METALS BY ICP-MS

Selenium (Se) 306 ug/L EPA 200.8 15-Sep-11 13:43 KRICHAR 10

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) < 10 ug/L EPA 200.8 19-Sep-11 10:30 DJSULL1 10

Chromium (Cr) < 10 ug/L EPA 200.8 19-Sep-11 10:30 DJSULL1 10

Copper (Cu) < 10 ug/L EPA 200.8 19-Sep-11 10:30 DJSULL1 10

Nickel (Ni) 35.5 ug/L EPA 200.8 19-Sep-11 10:30 DJSULL1 10

Selenium (Se) 336 ug/L EPA 200.8 19-Sep-11 10:30 DJSULL1 10

Silver (Ag) < 10 ug/L EPA 200.8 19-Sep-11 10:30 DJSULL1 10

Zinc (Zn) < 20 ug/L EPA 200.8 19-Sep-11 10:30 DJSULL1 20

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

2011019123

Collection Date: 14-Sep-11 7:45 AM

Site: BIOREACTOR 2 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 154 mg/L EPA 200.7 16-Sep-11 10:40 DJSULL1 0.5

Analytical Lab 

Page 5 of 27
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11090012

2011019123

Collection Date: 14-Sep-11 7:45 AM

Site: BIOREACTOR 2 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) < 10 ug/L EPA 200.8 19-Sep-11 10:33 DJSULL1 10

Chromium (Cr) < 10 ug/L EPA 200.8 19-Sep-11 10:33 DJSULL1 10

Copper (Cu) < 10 ug/L EPA 200.8 19-Sep-11 10:33 DJSULL1 10

Nickel (Ni) < 10 ug/L EPA 200.8 19-Sep-11 10:33 DJSULL1 10

Selenium (Se) 29.9 ug/L EPA 200.8 19-Sep-11 10:33 DJSULL1 10

Silver (Ag) < 10 ug/L EPA 200.8 19-Sep-11 10:33 DJSULL1 10

Zinc (Zn) < 20 ug/L EPA 200.8 19-Sep-11 10:33 DJSULL1 20

2011019124

Collection Date: 14-Sep-11 7:50 AM

Site: BIOREACTOR 2 EFF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

INORGANIC IONS BY IC

Bromide 83 mg/L EPA 300.0 22-Sep-11 20:27 CLEEMAN 10

MERCURY (COLD VAPOR) IN WATER

Mercury (Hg) < 1 ug/L EPA 245.1 16-Sep-11 09:10 AGIBBS 1

TOTAL RECOVERABLE METALS BY ICP

Boron (B) 159 mg/L EPA 200.7 16-Sep-11 10:44 DJSULL1 0.5

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) < 10 ug/L EPA 200.8 19-Sep-11 10:36 DJSULL1 10

Chromium (Cr) < 10 ug/L EPA 200.8 19-Sep-11 10:36 DJSULL1 10

Copper (Cu) < 10 ug/L EPA 200.8 19-Sep-11 10:36 DJSULL1 10

Nickel (Ni) 17.1 ug/L EPA 200.8 19-Sep-11 10:36 DJSULL1 10

Selenium (Se) < 10 ug/L EPA 200.8 19-Sep-11 10:36 DJSULL1 10

Silver (Ag) < 10 ug/L EPA 200.8 19-Sep-11 10:36 DJSULL1 10

Zinc (Zn) < 20 ug/L EPA 200.8 19-Sep-11 10:36 DJSULL1 20

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

2011019125

Collection Date: 14-Sep-11 8:00 AM

Site: FILTER BLANK 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

DISSOLVED METALS BY ICP-MS

Selenium (Se) < 1 ug/L EPA 200.8 15-Sep-11 13:19 KRICHAR 1

Analytical Lab 

Page 6 of 27
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11090012

2011019126

Collection Date: 01-Sep-11 10:30 AM

Site: Trip Blank 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

TOTAL RECOVERABLE METALS BY ICP

Boron (B) < 0.05 mg/L EPA 200.7 16-Sep-11 09:33 DJSULL1 0.05

TOTAL RECOVERABLE METALS BY ICP-MS

Arsenic (As) < 1 ug/L EPA 200.8 19-Sep-11 09:54 DJSULL1 1

Chromium (Cr) < 1 ug/L EPA 200.8 19-Sep-11 09:54 DJSULL1 1

Copper (Cu) < 1 ug/L EPA 200.8 19-Sep-11 09:54 DJSULL1 1

Nickel (Ni) < 1 ug/L EPA 200.8 19-Sep-11 09:54 DJSULL1 1

Selenium (Se) < 1 ug/L EPA 200.8 19-Sep-11 09:54 DJSULL1 1

Silver (Ag) < 1 ug/L EPA 200.8 19-Sep-11 09:54 DJSULL1 1

Zinc (Zn) < 2 ug/L EPA 200.8 19-Sep-11 09:54 DJSULL1 2

SELENIUM SPECIATION

Vendor Parameter Complete V_AS&C

2011019127

Collection Date: 14-Sep-11 12:55 PM

Site: BIOREACTOR 1 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY 1631

Vendor Parameter Complete V_BRAND

2011019128

Collection Date: 14-Sep-11 12:55 PM

Site: HG BLANK BIOREACTOR 1 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY 1631

Vendor Parameter Complete V_BRAND

2011019129

Collection Date: 14-Sep-11 1:15 PM

Site: BIOREACTOR 2 INF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY 1631

Vendor Parameter Complete V_BRAND

Analytical Lab 

Page 7 of 27
Certificate of Laboratory Analysis

This report shall not be reproduced, except in full.

Order # J11090012

2011019130

Collection Date: 14-Sep-11 1:15 PM

Site: Hg Blk BioReactor 2 Inf 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY 1631

Vendor Parameter Complete V_BRAND

2011019131

Collection Date: 14-Sep-11 1:00 PM

Site: BIOREACTOR 2 EFF. 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY 1631

Vendor Parameter Complete V_BRAND

2011019132

Collection Date: 14-Sep-11 1:00 PM

Site: Hg Blk BioReactor 2 Eff 

Matrix: OTHER

Analyte Result Units Qualifiers RDL Method Analysis Date/Time

Sample #:

Analyst

MERCURY 1631

Vendor Parameter Complete V_BRAND

Analytical Lab 

Page 8 of 27
 

September 23, 2011 

Jay Perkins 

Duke Energy Analytical Laboratory 

Mail Code MGO3A2 (Building 7405) 

13339 Hagers Ferry Rd. 

Huntersville, NC 28078 

(704) 875-5245 

Project: Belews – FGD WWTS Bi-Monthly Sampling (LIMS # J11090012) 

Dear Mr. Perkins, 

Attached is the report associated with four (4) aqueous samples submitted for selenium 

speciation analysis on September 15, 2011. The samples were received on September 16, 2011 

in a sealed cooler at -0.5oC. Selenium speciation analysis was performed via ion 

chromatography inductively coupled plasma dynamic reaction cell mass spectrometry (IC-ICPDRC-MS). Any issues associated with the analysis are addressed in the following report. 

If you have any questions, please feel free to contact me at your convenience. 

 Sincerely, 

 

 Ben Wozniak

 Project Manager 

 Applied Speciation and Consulting, LLC 

 

Analytical Lab 

Page 9 of 27
Applied Speciation and Consulting, LLC 

Report prepared for: 

Jay Perkins 

Duke Energy Analytical Laboratory 

Mail Code MGO3A2 (Building 7405) 

13339 Hagers Ferry Rd. 

Huntersville, NC 28078 

Project: Belews – FGD WWTS Bi-Monthly Sampling (LIMS # J11090012) 

September 23, 2011 

1. Sample Reception 

Four (4) aqueous samples in 125mL HDPE bottles (provided by Applied Speciation and 

Consulting) were submitted for selenium speciation analysis on September 15, 2011. The 

samples were received on September 16, 2011 in a sealed container at -0.5

oC.

The samples were received in a laminar flow clean hood void of trace metals contamination 

and ultra-violet radiation. Upon reception, the samples were designated discrete sample 

identifiers. An aliquot of each sample was filtered (0.45μm) and these filtrates were stored in 

a secure, monitored cryofreezer (maintained at a temperature of -80oC) until selenium 

speciation analysis could be performed via ion chromatography inductively coupled plasma 

dynamic reaction cell mass spectrometry (IC-ICP-DRC-MS). 

2. Sample Preparation 

All sample preparation is performed in laminar flow clean hoods known to be free from trace 

metals contamination. All applied water for dilutions and sample preservatives are 

monitored for contamination to account for any biases associated with the sample results. 

Selenium Speciation Analysis by IC-ICP-DRC-MS Prior to analysis, an aliquot of each 

sample was filtered with a syringe filter (0.45μm) and injected directly into a sealed 

autosampler vial. No further sample preparation was performed as any chemical alteration of 

the samples may shift the equilibrium of the system resulting in changes in speciation ratios. 

3. Sample Analysis 

All sample analysis is preceded by a minimum of a five-point calibration curve spanning the 

entire concentration range of interest. Calibration curves are performed at the beginning of 

Analytical Lab 

Page 10 of 27
each analytical day. All calibration curves, associated with each species of interest, are 

standardized by linear regression resulting in a response factor. All sample results are 

instrument blank corrected to account for any operational biases associated with the 

analytical platform. 

Prior to sample analysis, all calibration curves are verified using second source standards 

which are identified as initial calibration verification standards (ICV). 

Ongoing instrument performance is identified by the analysis of continuing calibration 

verification standards (CCV) and continuing calibration blanks (CCB) at a minimal interval 

of every ten analytical runs. 

Selenium Speciation Analysis by IC-ICP-DRC-MS All samples for selenium speciation 

analysis were analyzed by ion chromatography inductively coupled plasma dynamic reaction 

cell mass spectrometry (IC-ICP-DRC-MS) on September 22, 2011. An aliquot of each 

sample is injected onto an anion exchange column and mobilized by a basic (pH > 7) 

gradient. The eluting selenium species are then introduced into a radio frequency (RF) 

plasma where energy-transfer processes cause desolvation, atomization, and ionization. The 

ions are extracted from the plasma through a differentially-pumped vacuum interface and 

travel through a pressurized chamber (DRC) containing a specific reactive gas which 

preferentially reacts with interfering ions of the same target mass to charge ratios (m/z). A 

solid-state detector detects ions transmitted through the mass analyzer and the resulting 

current is processed by a data handling system. 

Retention times for each eluting species are compared to known standards for species 

identification. 

4. Analytical Issues 

The overall analyses went well and no significant analytical issues were encountered. All 

quality control parameters associated with this sample were within acceptance limits.

The estimated method detection limits (eMDLs) for selenite, selenate, and selenocyanate are 

generated from replicate analyses of the lowest standard in the calibration curve. Not all 

selenium species are present in preparation blanks; therefore, eMDL calculations based on 

preparation blanks are artificially biased low. 

The eMDL for methylseleninic acid and selenomethionine is calculated from the average 

eMDL of selenite, selenate, and selenocyanate. The calibration does not contain 

methylseleninic acid or selenomethionine due to impurities in these standards which would 

bias the results for other selenium species. 

Analytical Lab 

Page 11 of 27
If you have any questions or concerns regarding this report, please feel free to contact me. 

Sincerely, 

Ben Wozniak 

Project Manager 

Applied Speciation and Consulting, LLC 

Analytical Lab 

Page 12 of 27
Sample Results

Sample ID Se(IV) Se(VI) SeCN MeSe(IV) SeMe

Unknown Se 

Species (n)

FGD Purge Eff 32.2 996 ND (<4.4) ND (<3.7) ND (<3.7) 0 (0)

BioReactor 1 Inf 26.1 226 ND (<1.1) 1.82 ND (<0.92) 0 (0)

BioReactor 2 Eff ND (<0.50) ND (<1.2) ND (<1.1) ND (<0.92) ND (<0.92) 0 (0)

Metals Trip Blk ND (<0.10) ND (<0.23) ND (<0.22) ND (<0.18) ND (<0.18) 0 (0)

All results reflect the applied dilution and are reported in μg/L

ND = Not detected at the applied dilution

SeCN = Selenocyanate

MeSe(IV) = Methylseleninic acid

SeMe = Selenomethionine

Unknown Se Species = Total concentration of all unknown Se species observed by IC-ICP-MS

n = number of unknown Se species observed

Report Generated by: Ben Wozniak

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Belews – FGD WWTS Bi-Monthly Sampling

Contact: Jay Perkins

Date: September 23, 2011

LIMS #J11090012

Analytical Lab 

Page 13 of 27
Quality Control Summary - Preparation Blank Summary

Analyte (μg/L) PBW1 PBW2 PBW3 PBW4 Mean StdDev eMDL* eMDL 10x eMDL 50x eMDL 200x

Se(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.010 0.10 0.50 2.0

Se(VI) 0.000 0.000 0.000 0.000 0.000 0.000 0.023 0.23 1.2 4.6

SeCN 0.000 0.000 0.000 0.000 0.000 0.000 0.022 0.22 1.1 4.4

MeSe(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.018 0.18 0.92 3.7

SeMe 0.000 0.000 0.000 0.000 0.000 0.000 0.018 0.18 0.92 3.7

eMDL = Estimated Method Detection Limit

*Please see narrative regarding eMDL calculations

Quality Control Summary - Certified Reference Materials

Analyte (μg/L) CRM True Value Result Recovery

Se(IV) LCS 9.57 9.742 101.8

Se(VI) LCS 9.48 9.328 98.4

SeCN LCS 8.92 8.897 99.7

MeSe(IV) LCS 6.47 5.890 91.0

SeMe LCS 9.32 8.826 94.7

Report Generated by: Ben Wozniak

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Belews – FGD WWTS Bi-Monthly Sampling

Contact: Jay Perkins

LIMS #J11090012

Date: September 23, 2011

Analytical Lab 

Page 14 of 27
Quality Control Summary - Matrix Duplicates

Analyte (μg/L) Sample ID Rep 1 Rep 2 Mean RPD

Se(IV) Batch QC* 270.7 277.8 274.3 2.6

Se(VI) Batch QC* 53.6 56.2 54.9 4.7

SeCN Batch QC* 19.5 20.6 20.0 5.9

MeSe(IV) Batch QC* 5.5 5.9 5.7 6.0

SeMe Batch QC* ND (<3.7) ND (<3.7) NC NC

ND = Not detected at the applied dilution

NC = Value was not calculated due to one or more concentrations below the eMDL

* Batch QC performed on sample from LIMS #J11090278

Quality Control Summary - Matrix Spike/ Matrix Spike Duplicate

Analyte (μg/L) Sample ID Spike Conc MS Result Recovery Spike Conc MSD Result Recovery RPD

Se(IV) Batch QC* 1112 1444 105.1 1112 1437 104.5 0.5

Se(VI) Batch QC* 1009 1066 100.2 1009 1043 98.0 2.2

SeCN Batch QC* 915.0 869.7 92.9 915.0 873.5 93.3 0.4

* Batch QC performed on sample from LIMS #J11090278

Date: September 23, 2011

Report Generated by: Ben Wozniak

Applied Speciation and Consulting, LLC

Selenium Speciation Results for Duke Energy

Project Name: Belews – FGD WWTS Bi-Monthly Sampling

Contact: Jay Perkins

LIMS #J11090012

Analytical Lab 

Page 15 of 27
Analytical Lab 

Page 16 of 27
 

3958 6th Ave NW • Seattle, WA 98107 • T: 206-632-6206 • F: 206-632-6017 • www.brooksrand.com • brl@brooksrand.com 

September 23, 2011 

Duke Energy 

ATTN: Jay Perkins 

Scientific Support-Laboratory

13339 Hagers Ferry Road 

Huntersville NC 28078 

jcperkins@duke-energy.com 

labcustomer@duke-energy.com 

RE: Project DUK-HV1101 Client Project: J11090012 

Dear Mr. Perkins, 

On September 16, 2011, Brooks Rand Labs (BRL) received three (3) flue gas desulfurization 

(FGD) waste water samples and three (3) corresponding field blanks. Samples were logged-in 

for total mercury (Hg) analysis. All samples were received, prepared, analyzed, and stored 

according to BRL SOPs and EPA methodology. 

The results were blank-corrected as described in the calculations section of the applicable 

SOP(s) and may be evaluated using adjusted reporting limits to account for sample aliquot size. 

Please refer to the Sample Results page for sample-specific detection limits and other details. 

All other quality assurance criteria were satisfied and, aside from concentration qualifiers, all 

data was reported without additional qualification. 

BRL, an accredited laboratory, certifies the reported results of all analyses for which BRL is 

NELAP accredited meet all NELAP requirements. For more details, see the Report Information

page of the report. 

Please feel free to contact me if you have any questions regarding this report. 

Sincerely, 

 

Lydia Greaves 

Project Manager 

lydia@brooksran.com 

Analytical Lab 

Page 17 of 27
Project ID: DUK-HV1101

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Definition of Data Qualifiers

(Effective 9/23/09)

Laboratory Accreditation

BRL is accredited by the National Environmental Laboratory Accreditation Program (NELAP) through the State of Florida 

Department of Health, Bureau of Laboratories (E87982) and is certified to perform many environmental analyses. BRL is 

also certified by many other states to perform environmental analyses. For a current list of our accreditations /certifications, 

please visit our website at <http://www.brooksrand.com/default.asp?contentID=586>. Results reported relate only to the 

samples listed in the report.

Report Information

BLK

BRL

BS

CAL

CCV

CRM

D

DUP

ICV

MSD

ND

NR

PS

REC

RPD

RSD

SCV

SOP

method blank 

Brooks Rand Labs

laboratory fortified blank

calibration standard

continuing calibration verification

certified reference material

dissolved fraction

duplicate

initial calibration verification

matrix spike duplicate

non-detect

non-reportable

post preparation spike

percent recovery

relative percent difference

relative standard deviation

secondary calibration verification

standard operating procedure

MDL

MRL

MS

method detection limit

method reporting limit

matrix spike

SRM

T

COC

standard reference material

total recoverable fraction

chain of custody record 

Common Abbreviations

These qualifiers are based on those previously utilized by Brooks Rand, Ltd., those found in the EPA SOW ILM03.0, 

Exhibit B, Section III, pg. B-18, and the USEPA Laboratory Data Validation Functional Guidelines for Evaluating Inorganic 

Analyses; USEPA; July 2002. These supersede all previous qualifiers ever employed by BRL.

B Detected by the instrument, the result is > the MDL but ≤ the MRL. Result is reported and considered an estimate.

E An estimated value due to the presence of interferences. A full explanation is presented in the narrative.

H Holding time and/or preservation requirements not met. Result is estimated.

J Estimated value. A full explanation is presented in the narrative.

J-M Duplicate precision (RPD) for associated QC sample was not within acceptance criteria. Result is estimated.

J-N Spike recovery for associated QC sample was not within acceptance criteria. Result is estimated.

M Duplicate precision (RPD) was not within acceptance criteria. Result is estimated.

N Spike recovery was not within acceptance criteria. Result is estimated.

R Rejected, unusable value. A full explanation is presented in the narrative.

U Result is ≤ the MDL or client requested reporting limit (CRRL). Result reported as the MDL or CRRL.

X Result is not BLK-corrected and is within 10x the absolute value of the highest detectable BLK in the batch. 

Result is estimated.

Field Quality Control Samples

Please be notified that certain EPA methods require the collection of field quality control samples of an appropriate type 

and frequency; failure to do so is considered a deviation from some methods and for compliance purposes should only be 

done with the approval of regulatory authorities. Please see the specific EPA methods for details regarding required field 

quality control samples.

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Analytical Lab 

Page 18 of 27
Project ID: DUK-HV1101

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Sample Information

Sample Lab ID Report Matrix Type Sampled Received

BioReactor 1 Inf 1138040-01 FGD Wastewater Sample 09/14/2011 09/16/2011

Hg Blk BioReactor 1 Inf 1138040-02 DIW Field Blank 09/14/2011 09/16/2011

BioReactor 2 Inf 1138040-03 FGD Wastewater QC Sample 09/14/2011 09/16/2011

Hg Blk BioReactor 2 Inf 1138040-04 DIW Field Blank 09/14/2011 09/16/2011

BioReactor 2 Eff 1138040-05 FGD Wastewater Sample 09/14/2011 09/16/2011

Hg Blk BioReactor 2 Eff 1138040-06 DIW Field Blank 09/14/2011 09/16/2011

Batch Summary

Analyte Lab Matrix Method Prepared Analyzed Batch Sequence

Hg Water EPA 1631 09/20/2011 09/22/2011 B111468 1100653

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Analytical Lab 

Page 19 of 27
Project ID: DUK-HV1101

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Sample Results

Sample Analyte Report Matrix Fraction Result Qualifier MDL MRL Unit Batch Sequence

BioReactor 1 Inf

1138040-01 Hg FGD Wastewater T 398 1.52 4.04 ng/L B111468 1100653

BioReactor 2 Eff

1138040-05 Hg FGD Wastewater T 50.8 0.60 1.59 ng/L B111468 1100653

BioReactor 2 Inf

1138040-03 Hg FGD Wastewater T 100 0.59 1.58 ng/L B111468 1100653

Hg Blk BioReactor 1 Inf

1138040-02 Hg DIW T 0.15 U 0.15 0.40 ng/L B111468 1100653

Hg Blk BioReactor 2 Eff

1138040-06 Hg DIW T 0.15 U 0.15 0.40 ng/L B111468 1100653

Hg Blk BioReactor 2 Inf

1138040-04 Hg DIW T 0.15 U 0.15 0.41 ng/L B111468 1100653

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Analytical Lab 

Page 20 of 27
Project ID: DUK-HV1101

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Accuracy & Precision Summary

Analyte Native Spike Result Units REC & Limits RPD & Limits

Batch: B111468

Method: EPA 1631

Lab Matrix: Water

Sample

B111468-SRM1 Certified Reference Material (1137004, NIST 1641d 1000x dilution)

Hg 15.68 16.70 ng/L 107% 85-115

B111468-MS3 Matrix Spike (1138040-03)

Hg 99.95 244.3 377.3 ng/L 114% 71-125

B111468-MSD3 Matrix Spike Duplicate (1138040-03)

Hg 99.95 236.9 368.5 ng/L 113% 71-125 242%

Method Blanks & Reporting Limits

Batch: B111468

Method: EPA 1631

Matrix: Water

Analyte: Hg

Sample Result Units

B111468-BLK1 0.08 ng/L

B111468-BLK2 0.009 ng/L

B111468-BLK3 0.10 ng/L

B111468-BLK4 0.05 ng/L

Average: 0.06 Standard Deviation: 0.04 MDL: 0.15

Limit: 0.50 Limit: 0.10 MRL: 0.41

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Analytical Lab 

Page 21 of 27
Project ID: DUK-HV1101

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Instrument Calibration

Sequence: 1100653

Instrument: THG-05 Method: EPA 1631

Date: 09/22/2011

Total Mercury and Mercury Speciation by CVAFS

Analyte: Hg

Lab ID True Value Result Units REC & Limits

1100653-IBL1 4.37 pg of Hg

1100653-IBL2 7.01 pg of Hg

1100653-IBL3 7.31 pg of Hg

1100653-IBL4 5.95 pg of Hg

1100653-CAL1 25.00 24.48 pg of Hg 98%

1100653-CAL2 100.0 96.32 pg of Hg 96%

1100653-CAL3 500.0 505.5 pg of Hg 101%

1100653-CAL4 2500 2592 pg of Hg 104%

1100653-CAL5 10000 10130 pg of Hg 101%

1100653-ICV1 1568 1670 pg of Hg 107% 85-115

1100653-CCB1 7.17 pg of Hg

1100653-CCV1 500.0 472.9 pg of Hg 95% 77-123

1100653-CCV2 500.0 493.2 pg of Hg 99% 77-123

1100653-CCV3 500.0 440.9 pg of Hg 88% 77-123

1100653-CCV4 500.0 422.7 pg of Hg 85% 77-123

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Analytical Lab 

Page 22 of 27
Project ID: DUK-HV1101

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Sample Containers

Lab ID: 1138040-01 Report Matrix: FGD Wastewater

Sample: BioReactor 1 Inf Sample Type: Sample Received: 09/16/2011

Collected: 09/14/2011

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71313080

60

Cardboard 

Box

Bottle FLPE Hg-T 250 mL None N/A

Lab ID: 1138040-02 Report Matrix: DIW

Sample: Hg Blk BioReactor 1 Inf Sample Type: Field Blank Received: 09/16/2011

Collected: 09/14/2011

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71313080

60

Cardboard 

Box

Bottle FLPE Hg-T 250 mL None N/A

Lab ID: 1138040-03 Report Matrix: FGD Wastewater

Sample: BioReactor 2 Inf Sample Type: QC Sample Received: 09/16/2011

Collected: 09/14/2011

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71313080

60

Cardboard 

Box

Bottle FLPE Hg-T 250 mL None N/A

Lab ID: 1138040-04 Report Matrix: DIW

Sample: Hg Blk BioReactor 2 Inf Sample Type: Field Blank Received: 09/16/2011

Collected: 09/14/2011

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71313080

60

Cardboard 

Box

Bottle FLPE Hg-T 250 mL None N/A

Lab ID: 1138040-05 Report Matrix: FGD Wastewater

Sample: BioReactor 2 Eff Sample Type: Sample Received: 09/16/2011

Collected: 09/14/2011

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71313080

60

Cardboard 

Box

Bottle FLPE Hg-T 250 mL None N/A

Lab ID: 1138040-06 Report Matrix: DIW

Sample: Hg Blk BioReactor 2 Eff Sample Type: Field Blank Received: 09/16/2011

Collected: 09/14/2011

Des Container Size Lot Preservation P-Lot pH Ship. Cont.

A 71313080

60

Cardboard 

Box

Bottle FLPE Hg-T 250 mL None N/A

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Analytical Lab 

Page 23 of 27
Project ID: DUK-HV1101

PM: Tiffany Stilwater

Client PM: Jay Perkins

 Client PO: 141391

Shipping Containers

Cardboard Box

Tracking No: 4726 7966 3940 via FedEx

Temperature: ambient

Coolant Type: None

Description: Cardboard Box

Damaged in transit? No

Returned to client? No

Custody seals present? Yes

Custody seals intact? Yes

COC present? Yes

Received: September 16, 2011 9:00

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

Analytical Lab 

Page 24 of 27
Analytical Lab 

Page 25 of 27
Analytical Lab 

Page 26 of 27
Analytical Lab 

Page 27 of 27