Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Saturday, January 22, 2011 Page 1 of 11
Facility Information:

Central Power and Lime, Inc.

10311 Cement Plant Road

Brooksville FL 34605

Contact: Larry Roberts

Phone: 352-799-7881

Fax:

Email: Lroberts@deltapowerservices.com

Testing Company:

Koogler and Associates, Inc.

4014 NW 13th St

Gainesville FL 32609

Contact: Dr. Max Lee

Phone: 352-377-5822

Fax:

Email: mlee@kooglerassociates.com

Air Permit Number:

0530021-011-AV

Permitted Source ID/Name:

1 Boiler

Permitted Maximum Process Rate:

150 MW

Max. Normal Operation Process Rate:

150 MW

Target Process Test Rate

135 MW

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Power Plant Boiler with Dry Limestone Injection Scrubbing follwed with a Baghouse System. The emissions unit is 

a net delivered 150MW fossil fuel fired boiler with a 320 foot stack. The primary fuel burned is coal, with new 

distillate No. 2 fuel oil used for startup. Control activity includes dru limestone injection scrubbing followed with a 

fabric filter baghouse system. The exit diameter is 16 feet and exit temperature is 300 degrees F. The volumetric flow 

rate is 840,000 acfm.

Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Power Plant 

Duct

0 144 144 0 0 0 1 1

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Power Plant Carbon Monoxide Method 10 3 120 0

Duct

Total organic compounds 

(TOC) as Methane

Method 25A 3 120 0 Only For the Method 

25A -CH4 Runs

Power Plant 

Duct

Saturday, January 22, 2011 Page 2 of 11
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 0 For Method 25A runs 

1-3

Power Plant 

Duct

Power Plant O2 Method 3A O2 3 120 0

Duct

Saturday, January 22, 2011 Page 3 of 11
Sampling / Stack Data Results Summary

Location Power Plant Duct - Method 10

Average

Run Number

Test Date 14 13.9 13.9

Run Start Time

Run Finish Time 7.1 7.2 7.3

Carbon Dioxide, % 1500 1500 1500 1,500.000

Oxygen, % 10 0 0 3.333

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2 Power Plant 

Duct

Power 

Plant Duct

Power Plant 

Duct

Moisture, % 48 48 48 48.000

Fuel Type

Fw Method 10 Method 10 Method 10

Fc 1 2 3 2.000

Location Power Plant Duct - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, January 22, 2011 Page 4 of 11
Location Power Plant Duct - Method 25A 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Power Plant Duct - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Saturday, January 22, 2011 Page 5 of 11
Emissions Summary

Process Run Data

Location: Power Plant Duct - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 5.20E-01 5.90E-01 5.16E-01 0.542

ppm 4.83E+02 5.44E+02 4.72E+02 499.667

ppm@7%O2 4.87E+02 5.52E+02 4.82E+02 507.000

Location: Power Plant Duct - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 -6.02E-06 6.37E-06 -2.16E-04 0.000

ppm -9.90E-03 1.04E-02 -3.53E-01 -0.118

ppm@7%O2 -9.83E-03 1.04E-02 -3.53E-01 -0.117

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 -1.65E-05 1.75E-05 -5.94E-04 0.000

ppm -9.90E-03 1.04E-02 -3.53E-01 -0.118

ppm@7%O2 -9.83E-03 1.04E-02 -3.53E-01 -0.117

Location: Power Plant Duct - Method 25A 3

Compound: Total organic compounds (TOC) as 

Average

Run CH4-1 CH4-2 CH4-3

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ppm 0.00E+00 0.00E+00 0.00E+00 0.000

ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total organic compounds (TOC) as 

Average

Run CH4-1 CH4-2 CH4-3

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ppm 0.00E+00 0.00E+00 0.00E+00 0.000

ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Saturday, January 22, 2011 Page 6 of 11
Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Generator Rate 136.4 MW 135

1 Heat Input 1409 Million Btus/hr 1400

1 Coal Feed Rate 55.1 TPH 55

2 Generator Rate 135.4 MW 135

2 Heat Input 1419 Million Btus/hr 1400

2 Coal Feed Rate 55.5 TPH 55

3 Generator Rate 136.1 MW 135

3 Heat Input 1423 Million Btus/hr 1400

3 Coal Feed Rate 55.7 TPH 55

Run Name Value UOM Comments

Target

Value

1 DRY LIMESTONE INJECTION 20.92 0

2 DRY LIMESTONE INJECTION 20.92 0

3 DRY LIMESTONE INJECTION 20.92 0

1 BAGHOUSE 0 0

2 BAGHOUSE 0 0

3 BAGHOUSE 0 0

Saturday, January 22, 2011 Page 7 of 11
Sampling / Stack Data Results Detail

Location Power Plant Duct - Method 10

Average

Run Number

Test Date 14 13.9 13.9

Run Start Time

Run Finish Time 7.1 7.2 7.3

Carbon Dioxide, % 1500 1500 1500 1,500.000

Oxygen, % 10 0 0 3.333

Fuel Factor 8/31/2010 8/31/2010 8/31/2010

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2 Power Plant 

Duct

Power Plant 

Duct

Power Plant 

Duct

Moisture, % 48 48 48 48.000

Analyzer Make 1 1 1 1.000

Analyzer Model Nitrogen Nitrogen Nitrogen

Analyzer Serial Number 1.36 0 0 0.453

Operating Range -99.81 -99.92 -99.92 -99.883

Operating Units 0 0 0

No. Readings/Avg. CO Mid CO Mid CO Mid

Calibration Set -0.5 -1.4 -1.59 -1.163

Calibration Pre Zero Cylinder ID 0 0 0

Calibration Pre Zero Cylinder Instrument Response Nitrogen Nitrogen Nitrogen

Calibration Pre Zero Cylinder Bias 0 0 0 0.000

Calibration Pre Zero Cylinder Drift -99.92 -99.92 -99.92 -99.920

Calibration Pre High Cylinder ID 0.1099999999

99999

0 0

Calibration Pre High Cylinder Instrument Response CO Mid CO Mid CO Mid

Calibration Pre High Cylinder Bias 426.6 424.3 425.2 425.367

Calibration Pre High Cylinder Drift -1.4 -1.59 -1.52 -1.503

Calibration Post Zero Cylinder ID 0.9 0.19 7.000000000

00001E-02

Calibration Post Zero Cylinder Instrument Response 464.7 515 446.4 475.367

Calibration Post Zero Cylinder Bias ppmvd ppmvd ppmvd

Calibration Post Zero Cylinder Drift 483.2556 543.749 472.0962 499.700

Calibration Post High Cylinder ID ppmvd ppmvd ppmvd

Calibration Post High Cylinder Instrument Response Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Calibration Post High Cylinder Bias 9780 9780 9780 9,780.000

Calibration Post High Cylinder Drift 10640 10640 10640 10,640.000

Cavg 1800 1800 1800 1,800.000

Cavg Units 0.99 1 0.98

Cgas 0 0 0 0.000

Cgas Units

Fuel Type

Fw Method 10 Method 10 Method 10

Fc 1 2 3 2.000

Cgasw 3:00:00 PM 5:25:00 PM 7:48:00 PM

Cgasw Units 5:00:00 PM 7:25:00 PM 9:48:00 PM

Saturday, January 22, 2011 Page 8 of 11
Location Power Plant Duct - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 9 of 11
Location Power Plant Duct - Method 25A 3

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 10 of 11
Location Power Plant Duct - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Saturday, January 22, 2011 Page 11 of 11