# EMISSIONS TEST REPORT

POLK POWER STATION FACILITY ID NUMBER: 1050233 EMISSION UNIT ID NO: -001 UNIT 1 SYNTHETIC GAS

CARBON MONOXIDE, VOLATI LE ORGANIC COMPOUNDS, SULFURIC ACID MIST, VISIBL E EMISSIONS EVALUATION, and OXIDES OF NITROGEN, SULF UR DIOXIDE FROM CEMS

December 15 & 16, 2008

Prepared For: Tampa Electric Company Polk Power Station P.O. Box 111 Tampa, Florida 33601-0111

Prepared By: Tampa Electric Company Environmental, Health, & Safety Air Services Group

Environmental, Health, & Safety Air Services Group 5010 Causeway Boulevard Tampa, Florida 33619- 6130

## REPORT CERTIFICATION

The sampling and subseque nt data entry/reduction detailed in this report was conducted at my direction, and I here by certify that this test report is authentic and accurate to the best of my knowledge.

Signature:__________________________ Jorge A. Varino Environmental Technician Test Team Lead Air Services Group Environmental Health & Safety Tampa Electric Company

I have reviewed the test performa nce, associated quality assurance activities, the resultant calculations, and the contents of this report, and certify that all project quality obj ectives have been met. Th is report is approved for submittal.

Signature:__________________________ Raymond A. McDarby, Jr. Senior Environmental Technician Quality Assurance/Quality Control Specialist Air Services Group Environmental Health & Safety Tampa Electric Company

I have reviewed the testing details and results submitted in this report, and hereby certify that this test report is authenti c and accurate to the best of my knowledge.

Signature:__________________________ David A. Smith, QSTI Coordinator – Air Services Group

Environmental Health & Safety Tampa Electric Company

## TABLE OF CONTENTS

SECTION PAGE NO. 1.0 INTRODUCTION 1 2.0 DISCUSSION OF RESULTS 2 3.0 SOURCE DESCRIPTION/TEST PROCEDURES 4 4.0 TABULATED RESULTS CARBON MONOXIDE TEST DATA 6 VOLATILE ORGANIC COMPOUND DATA 7 SULFURIC ACID MIST TEST DATA 8 NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 9 HEAT INPUT CALCULATIONS, DECEMBER 15, 2008 10 HEAT INPUT CALCULATIONS, DECEMBER 16, 2008 11 5.0 STACK SAMPLING LOCATION DIAGRAM 13

APPENDICES

A. CARBON MONOXIDE TEST INFORMATION SUMMARIZED RUN DATA & QA/QC TEST RUN LOG CYLINDER GAS CERTIFICATES
B. VOLATILE ORGANIC COMPOUNDS TEST DATA FIELD DATA SHEETS LABORATORY ANALYSIS – ENTHALPY ANALYTICAL, INC. C. SULFURIC ACID MIST TEST DATA FIELD DATA SHEETS CALCULATED RUN DATA LABORATORY ANALYSIS EQUIPMENT CALIBRATIONS
D. TURBINE DATA
E. FUEL ANALYSIS
F. CEMS DATA G. VISIBLE EMISSION DATA SHEET
H. TEST PARTICIPANTS

### 1 

## 1.0 INTRODUCTION

On December 15, and 16, 2008, Tampa Electr ic Company’s, Environmental Services, Air Services Group performed source emission tests, on Unit No. 1 at the Polk Power Station. The tests incl ude Carbon Monoxide (CO), Volatile Organic Compounds (VOCs), Sulfuric Acid Mist (SAM), and Visi ble Emissions Observations (VEOs). Unit No. 1 is a combined cycle combustion turbi ne generating unit. The combustion turbine was fired with syngas from the solid fuel gas ification system. A blend of petroleum coke and bituminous coal was gasified for this te st. Testing was conducted according to United States Environmental Protection Agency (USEPA) test methods stipulated in 40 CFR Part 60, Appendix A and Flor ida Department of Environm ental Protection (FDEP)
Permit No. 1050233-016-AV.

Nitrogen Oxides (NO x 

## ) and Sulfur Dioxide (SO 2 

## ) data was taken from the Continuous Emissions Monitoring System’s (CEMS) Da ta Acquisition and Handling System (DAHS) concurrent with the SAM testing, and is pr esented as averages over the test period.

### 2 

## 2.0 DISCUSSION OF RESULTS

Executive Summary Tampa Electric Company Polk Power Station General Electric 7F Combined Cycle Combustion Turbine Emission Unit ID -001

Solid Fuel Derived Synthetic Gas Compliance Parameter Test Result FDEP Permit Limit CO, ppmvd @15% O2 3 25 CO, lbs/hr 12 98 VOC, lbs/hr 41 3 SAM, lbs/hr 43 55 VE, % opacity 0 10 December 15, 2008 NOX, lbs/hr 106.30 220.25 SO2, lbs/hr 315 357 Heat Input, mmBtu/hr 1638 -- Maximum Heat Input 1 1751 -- Unit Load (% of permit) 2 94% 90 – 100% December 16, 2005 NOX, lbs/hr 103.59 220.25 SO2, lbs/hr 319 357 Heat Input, mmBtu/hr 1629 Maximum Heat Input 1 1752 Unit Load (% of permit) 2 93% 90 – 100%

1 Maximum Heat Input is Permitted Maximum Heat Input Rate, 1755 mmBtu/hr @ 59o F, Corrected to Average Ambient Temperature Recorded During the Test Period.



## 2 Unit Load (% of permit) is Heat Input Divided by Maximum Heat Input times 100.



## The Carbon Monoxide (CO) concentration and em ission rate was derived from three 1- hour Reference Method 10 test runs conduct ed on December 15, 2008. The calculated average CO concentration was 3 ppmvd @ 15% O 2 

## . The calculated average emission rate was 12 lbs/hr. The FDEP permitt ed concentration is 25 ppmvd @15% O 2 

## . The FDEP permitted emission rate is 98 lbs/hr based on a 30-day rolling average.

The Volatile Organic Compounds (VOCs) emi ssion rate was derived from three 1-hour Reference Method 18 test r uns conducted on December 15, 2008. The calculated average VOCs emission rate was 41 lbs/hr. The FDEP permitted emission rate is 3

### 3 

## lbs/hr based on a 30-day rolling average.

The Sulfuric Acid Mist (SAM) emission ra te was derived from six 1-hour Reference
Method 8 test runs conducted on December 15 and 16, 2008. T he calculated average SAM emission rate was 43 lbs/hr. The FDEP permitted emission rate is 55 lbs/hr based on a 30-day rolling average.

The Visible Emissions Observations (VEO ) yielded an average opacity of 0% for the 1- hour test. The FDEP permitted opacity is 10 percent.

During the SAM testing, the Nitrogen Oxides (NO x 

## ) average emission rate was 104.59 lbs/hr.

During the SAM testing, the Sulfur Dioxide (SO 2 

## ) average emission rate was 317 lbs/hr.

During the December 15 th 

## , test Unit No. 1 was operated at an average heat input of 1638 mmBtu/hr. The FDEP permitted heat i nput is 1755 mmBtu/hr, at an ambient temperature of 59o (corrected to 1751 mmBtu/hr based on an average inlet vane temperature of 75o F, and the manufacturer’s heat input correction curve for this unit). The unit operated at 94% of permitted capacity.

During the December 16 th 

## , test Unit No. 1 was operated at an average heat input of 1629 mmBtu/hr. The FDEP permitted heat i nput is 1755 mmBtu/hr, at an ambient temperature of 59o (corrected to 1751 mmBtu/hr based on an average inlet vane temperature of 70o F, and the manufacturer’s heat input correction curve for this unit). The unit operated at 93% of permitted capacity.

### 4 

## 3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generat ing Station is located at County Road 630 approximately 13 miles southwest of Bartow, Polk County, Florida. Unit No. 1 is a Combined Cycle Combustion Turbine generating unit, with a net capacity of 192 MW when fired with Syngas fuel. The source sampling location c onsists of a circular stack 19 feet in diameter with four sample ports located 90 degrees apart on the stack circumference. A diagram of the stack sampling locati on is included along wit h other pertinent information on the test site.

Carbon Monoxide sampling was performed in accordance with USEPA Reference Method 10 (40 CFR Part 60, Appendix A) “Determination of Carbon Monoxide Emissions From Stationary Sources”. Testing was performed using a Thermo
Environmental Instruments model 48C Carbon Monoxide Analyzer.

Volatile Organic Compound sampling wa s performed in accordance with USEPA Reference Method 18 “Measurement of Ga seous Organic Compound Emissions by Gas Chromatography”. Analysis was perform ed by Enthalpy Analytical, Inc.

Sulfuric Acid Mist sampling was perfo rmed in accordance with USEPA Reference Method 8 “Determination of Sulfuric Acid Mist and Sulfur Dioxide Emissions From Stationary Sources”.

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. This data was taken as 1-minute averages ov er the time frame consistent with the Sulfuric Acid Mist testing.

Plant operational data was taken from the Pl ant Information (PI) se rver system. Data captured included the minute average load, minute fuel flow, minute inlet vane temperature, and minute saturator readings.

### 5 

## 4.0 TABULATED RESULTS

## POLK POWER STATION CARBON MONOXIDE DAT A

CO % O 2 

### CO, ppmvd CO Run # Start Stop ppmvd volume @ 15% O 2 

### lbs/hr 1 10:56 11:56 5.30 12.08 3.55 12.66 2 12:16 13:16 5.19 12.05 3.46 12.36 3 13:29 14:29 5.05 12.08 3.38 12.06 Averages: 3.461 12.359 CO, ppmvd @ 15% O 2 

### is calculated as: CO, ppmvd x (5.9 / (20.9 - % O 2 

### , volume))

CO, lbs/hr is calculated as: CO, ppmvd x C f 

### x F d 

### x (20.9 / (20.9 - % O 2 

### , volume) x Heat Input

where: C f 

### = 7.27249E-08 lb/scf F d 

### = 8460 dscf/mmBtu Heat Input = 1638 mmBtu/hr

Test Times are Eastern Standard. Test Times RM Data Calculated Data 

## HEAT RECOVERY STEAM GENERATOR UNIT 1 December 15, 2008

6

## POLK POWER STATION V

OLATILE ORGANIC COMPOUNDS DAT A

THC, ppm VOC 

## Flow Rate VOC Run # Start Stop as C 6 

### H 14 

### lb/scf scf/hr lbs/hr 1 10:56 11:56 2.01 4.498E-07 4.890E+07 21.99 2 12:16 13:16 3.54 7.921E-07 4.899E+07 38.81 3 13:29 14:29 5.63 1.260E-06 4.900E+07 61.73 Averages: 40.844

VOC, lb/scf calculated as: ppm VOC x C f 

### where: C f



### = Mole wieght of hexane (86.18 lb/lb-mole) x 10 - 6 

### / (385.15 scf/lb-mole) 2.238E-07 lbs/dscf

VOC, lbs/hr calculated as: VOC, lb/scf x Stack Flow, scf/hr Test Times 

## HEAT RECOVERY STEAM GENERATOR UNIT 1 December 15, 2008

7Environmental ServicesAir Services Group40 CFR 60, Appendix A - Test MethodsReference Method 8Test SummaryCustomer: Polk Power StationFacility: Unit 1Sampling Location:StackOperating Conditions:Full LoadTest Date:Run #1Run #2Run #3Run #4Run #5Run #6AverageGas Flow RatesQs, acfm:1279774.1 1305033.2 1310020.0 1265799.8 1265685.7 1269097.6 1282568.4Qs(std), dscfm:817322.9 834220.4 836935.0 810020.3 810552.2 808202.2 819542.2Sampled Volume, Vm(std), dscf:36.98 37.66 37.80 36.95 36.57 36.7937.125Stack Moisture, Bwsx 100, %:5.98 5.81 5.68 5.56 5.22 5.775.670Isokinetic Sampling Rate, I, %:101 100.8 100.8 101.8 100.7 101.6101.12CH2SO4,lb/dscf:8.015E-07 1.237E-06 9.791E-07 5.615E-07 7.807E-07 8.102E-07 8.592E-07EH2SO4, lb/mmBtu:0.0206 0.0317 0.0251 0.0144 0.0200 0.02080.0221EH2SO4, lbs/hr:39624927383942December 15, 2008December 16, 20088

## POLK POWER STATION N O X 

## & S O 2 

## COMPLIANCE DATA FROM CEM S

NO x 

### SO 2 

### Flow NO x 

### SO 2 

### ppmvw ppmvw kscfmw lbs/hr lbs/hr

18.21 38.77 814.92 106.30 315

NO x 

### SO 2 

### Flow NO x 

### SO 2 

### ppmvw ppmvw kscfmw lbs/hr lbs/hr

17.78 39.43 813.25 103.59 319

NOX, lbs/hr calculated as: NOX, ppmvw x 1.194E-07 x Flow, kscfmw x 60 min/hr x 1000/k

SO2, lbs/hr calculated as: SO2, ppmvw x 1.660E-07 x Flow, kscfmw x 60 min/hr x 1000/k 

## HEAT RECOVERY STEAM GENERATOR UNIT 1 December 15, 2008

December 16, 2008

CEM Data Calculated Data CEM Data Calculated Data

9

## POLK POWER STATION HEAT INPUT CALCULATIO N

Average fuel flow: 6626.253 Kcfh M ole weight correction to meter cal: 0.9883 mole weight correction factor Corrected fuel flow:1 6548.7258 Kcfh, corrected for density Average moisture: 2.83 % H 2 

### 0 added to fuel Corrected fuel flow:2 6363.3492 Kscfh, corrected for moisture Gross heating value of fuel (HHV): 257.46 Btu/scf Heat Input: 1638 mmBtu/hr

Average fuel flow from Plant Information Data Base. Mole weight correction factor to meter calibrat ion is taken from ratio of syngas mole weight to calibration gas mole weight. 1Average fuel flow times mole weight correction factor. 2Corrected fuel flow times (1 - (Average moisture / 100)). Gross Heating value of fuel (HHV) is from fuel analysis. Heat input is (HHV x Corrected fuel flow) / 1000. 

## COMBINED CYCLE COMBUSTION TURBINE UNIT 1 December 15, 2008

10

## POLK POWER STATIO N HEAT INPUT CALCULATIO N

Average fuel flow: 6602.319 Kcfh Mole weight correction to meter cal: 0.9883 mole weight correction factor Corrected fuel flow:1 6525.0719 Kcfh, corrected for density Average moisture: 2.9 % H 2 

### 0 added to fuel Corrected fuel flow:2 6335.8448 Kscfh, corrected for moisture Gross heating value of fuel (HHV): 257.15 Btu/scf Heat Input: 1629 mmBtu/hr

Average fuel flow from Plant Information Data Base. Mole weight correction factor to meter calibration is taken from ratio of syngas mole weight to calibration gas mole weight. 1Average fuel flow times mole weight correction factor. 2Corrected fuel flow times (1 - (Average moisture / 100)). Gross Heating value of fuel (HHV) is from fuel analysis. Heat input is (HHV x Co rrected fuel flow) / 1000. 

## COMBINED CYCLE COMBUSTION TURBINE UNIT 1 December 16, 2008

11

### 12 

## 5.0 SAMPLING LOCATION DIAGRAM

### 13 UNFIRED HEAT

RECOVERY

BOILER TRANSITION

DUCT

EXHAUST FROM TURBINE 14 FT.

38 FT. 150 FT.

136 FT. 

## POLK POWER STATION COMBUSTION TURBINE COMBINED CYCLE UNIT NO.1 TEST LOCATION

PORT LOCATION PLAN 19.0 FT.ID.

STACK DIAMETERS DOWNSTREAM FROM DISTURBANCE = 2.0 STACK DIAMETERS UPSTREAM FROM DISTURBANCE = 0.7 STACK DIAMETER = 19.0 FT. STACK AREA = 283.529 S Q . FT. STACK AREA =40828.138 SQ. IN.

## APPENDIX A

CARBON MONOXIDE TEST INFORMATION

## SUMMARIZED RUN DATA & QA/QC

### LabView QA Data

Polk Unit 1 Compliance - Report RUN 1 12/15/2008 10:56:09 11:56:10

Analyzer Calibration Error (Eq 7E-1 ) aO2 bCO2 cCO Analyzer Range 25 20 10 Units % % PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.6 9.01 3.95 High Level Certified Value (PPM or %) 20.9 18 8.09 Zero Level Observed -0.002 -0.011 0.006 Low Level Observed - - - Mid Level Observed 10.564 9.001 3.97 High Level Observed 21.023 17.983 8.007 Zero Calibration Error ACE -0.01 -0.06 0.07 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE -0.17 -0.05 0.25 High Level Calibration Error ACE 0.59 -0.09 -1.03 Initial Readings Zero 0.031 0.039 0.009 Span 10.691 8.887 3.974 Final Readings Zero 0.095 0.029 -0.019 Span 10.607 8.823 3.964

System Bias (Eq 7E-2) Initial Zero Bias SB 0.16 0.28 0.04 Initial Span Bias SB 0.61 -0.63 0.05 Final Zero Bias SB 0.46 0.22 -0.31 Final Span Bias SB 0.21 -0.99 -0.07

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.15 0.22 0.11 Initial Span SCE 0.44 -0.68 0.3 Final Zero SCE 0.45 0.16 -0.23 Final Span SCE 0.03 -1.04 0.17

Drift Assessment (Eq 7E-4) Zero Drift D 0.3 0.06 0.35 Span Drift D 0.4 0.36 0.12

Effluent Gas Concentration (Eq 7E-5) Raw Results 12.13 8.81 5.33 Corrected Results (ppmv) 12.08 8.96 5.3

Page 1 of 3

### LabView QA Data

Polk Unit 1 Compliance - Report RUN 2 12/15/2008 12:16:44 13:16:44

Analyzer Calibration Error (Eq 7E-1 ) aO2 bCO2 cCO Analyzer Range 25 20 10 Units % % PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.6 9.01 3.95 High Level Certified Value (PPM or %) 20.9 18 8.09 Zero Level Observed -0.002 -0.011 0.006 Low Level Observed - - - Mid Level Observed 10.564 9.001 3.97 High Level Observed 21.023 17.983 8.007 Zero Calibration Error ACE -0.01 -0.06 0.07 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE -0.17 -0.05 0.25 High Level Calibration Error ACE 0.59 -0.09 -1.03 Initial Readings Zero 0.095 0.029 -0.019 Span 10.607 8.823 3.964 Final Readings Zero 0.098 0.034 0.019 Span 10.5 8.837 3.97

System Bias (Eq 7E-2) Initial Zero Bias SB 0.46 0.22 -0.31 Initial Span Bias SB 0.21 -0.99 -0.07 Final Zero Bias SB 0.48 0.25 0.16 Final Span Bias SB -0.31 -0.91 0

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.45 0.16 -0.23 Initial Span SCE 0.03 -1.04 0.17 Final Zero SCE 0.47 0.19 0.23 Final Span SCE -0.48 -0.96 0.25

Drift Assessment (Eq 7E-4) Zero Drift D 0.02 0.03 0.47 Span Drift D 0.52 0.08 0.07

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.98 8.79 5.21 Corrected Results (ppmv) 12.05 8.97 5.19

Page 2 of 3

### LabView QA Data

Polk Unit 1 Compliance - Report RUN 3 12/15/2008 13:29:24 14:29:25

Analyzer Calibration Error (Eq 7E-1 ) aO2 bCO2 cCO Analyzer Range 25 20 10 Units % % PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.6 9.01 3.95 High Level Certified Value (PPM or %) 20.9 18 8.09 Zero Level Observed -0.002 -0.011 0.006 Low Level Observed - - - Mid Level Observed 10.564 9.001 3.97 High Level Observed 21.023 17.983 8.007 Zero Calibration Error ACE -0.01 -0.06 0.07 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE -0.17 -0.05 0.25 High Level Calibration Error ACE 0.59 -0.09 -1.03 Initial Readings Zero 0.098 0.034 0.019 Span 10.5 8.837 3.97 Final Readings Zero 0.069 0.036 -0.02 Span 10.52 8.83 3.977

System Bias (Eq 7E-2) Initial Zero Bias SB 0.48 0.25 0.16 Initial Span Bias SB -0.31 -0.91 0 Final Zero Bias SB 0.34 0.26 -0.32 Final Span Bias SB -0.21 -0.95 0.09

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.47 0.19 0.23 Initial Span SCE -0.48 -0.96 0.25 Final Zero SCE 0.33 0.2 -0.25 Final Span SCE -0.38 -1 0.33

Drift Assessment (Eq 7E-4) Zero Drift D 0.14 0.01 0.48 Span Drift D 0.1 0.04 0.09

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.97 8.76 5.08 Corrected Results (ppmv) 12.08 8.93 5.05

Page 3 of 3

## TEST RUN LOGLabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 7:52:59 AM 20.54 0.02 0.51 12/15/2008 7:53:29 AM 20.54 0.02 0.53 12/15/2008 7:53:59 AM 20.5 0.05 0.36 12/15/2008 7:54:29 AM 20.55 0.09 0.36 12/15/2008 7:54:59 AM 20.63 0.09 0.28 12/15/2008 7:55:29 AM 20.67 0.1 0.32 12/15/2008 7:55:59 AM 20.69 0.1 0.3 12/15/2008 7:56:29 AM 20.7 0.1 0.29 12/15/2008 7:56:59 AM 20.74 0.1 0.31 12/15/2008 7:57:29 AM 20.74 0.1 0.28 12/15/2008 7:57:59 AM 20.74 0.11 0.29 12/15/2008 7:58:29 AM 20.74 0.1 0.31 12/15/2008 7:58:59 AM 20.75 0.1 0.27 12/15/2008 7:59:29 AM 20.76 0.11 0.31 12/15/2008 7:59:59 AM 20.75 0.11 0.28 12/15/2008 8:00:29 AM 21.03 0.11 0.28 12/15/2008 8:00:59 AM 21.05 0.11 0.3 12/15/2008 8:01:29 AM 21.05 0.11 0.3 12/15/2008 8:01:59 AM 21.04 0.11 0.33 12/15/2008 8:02:29 AM 21.05 0.11 0.31 12/15/2008 8:02:59 AM 20.14 0.11 0.3 12/15/2008 8:03:29 AM 20.2 0.11 0.33 12/15/2008 8:03:59 AM 21.05 0.11 0.27 12/15/2008 8:04:29 AM 21.08 0.06 0.22 12/15/2008 8:04:59 AM 21.12 -0.02 0.19 12/15/2008 8:05:29 AM 21.14 -0.03 0.15 12/15/2008 8:05:59 AM 21.15 -0.03 0.17 12/15/2008 8:06:29 AM 21.15 -0.01 0.18 12/15/2008 8:06:59 AM 21.16 -0.01 -0.01 12/15/2008 8:07:29 AM 21.17 -0.01 0.01 12/15/2008 8:07:59 AM Linearity Check 21.17 -0.01 -0.12 12/15/2008 8:08:29 AM Linearity Check 14.1 5.56 -0.46 12/15/2008 8:08:59 AM Linearity Check 10.67 9.44 -0.39 12/15/2008 8:09:29 AM Linearity Check 10.66 9.56 -0.36 12/15/2008 8:09:59 AM Linearity Check 10.66 8.8 -0.37 12/15/2008 8:10:29 AM Linearity Check 10.66 9 -0.38 12/15/2008 8:10:59 AM Linearity Check 10.65 9 -0.26 12/15/2008 8:11:29 AM Linearity Check 20.07 1.15 -0.05 12/15/2008 8:11:59 AM Linearity Check 20.07 0.03 2.85 12/15/2008 8:12:29 AM Linearity Check 20.07 0.27 8.34 12/15/2008 8:12:59 AM Linearity Check 20.07 0.16 4.87 12/15/2008 8:13:29 AM Linearity Check 20.07 0 4.76 12/15/2008 8:13:59 AM Linearity Check 20.07 0 4.73 12/15/2008 8:14:29 AM Linearity Check 20.07 -0.01 3.95 12/15/2008 8:14:59 AM Linearity Check 20.07 2.94 0.68 12/15/2008 8:15:29 AM Linearity Check 20.07 8.33 -0.28 12/15/2008 8:15:59 AM Linearity Check 20.07 8.97 -0.31 12/15/2008 8:16:29 AM Linearity Check 20.07 8.98 -0.29 12/15/2008 8:16:59 AM Linearity Check 10.55 9 -0.3 12/15/2008 8:17:29 AM Linearity Check 10.55 9 -0.31 12/15/2008 8:17:59 AM Linearity Check 12.43 9.77 -0.53 12/15/2008 8:18:29 AM Linearity Check 20.48 16.61 -0.59 12/15/2008 8:18:59 AM Linearity Check 21.02 17.96 -0.57 12/15/2008 8:19:29 AM Linearity Check 21.02 17.98 -0.6

Page 1 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 8:19:59 AM Linearity Check 21.03 17.99 -0.55 12/15/2008 8:20:29 AM Linearity Check 15.8 14.83 -0.31 12/15/2008 8:20:59 AM Linearity Check 10.6 9.28 -0.32 12/15/2008 8:21:29 AM Linearity Check 10.57 9.02 -0.28 12/15/2008 8:21:59 AM Linearity Check 10.56 9.01 -0.11 12/15/2008 8:22:29 AM Linearity Check 3.72 3.99 3.34 12/15/2008 8:22:59 AM Linearity Check 0.01 0.15 3.96 12/15/2008 8:23:29 AM Linearity Check 0 0.02 3.91 12/15/2008 8:23:59 AM Linearity Check 0 0.01 3.97 12/15/2008 8:24:29 AM Linearity Check 0 0.01 3.95 12/15/2008 8:24:59 AM Linearity Check 0 0 4.34 12/15/2008 8:25:29 AM Linearity Check 0 0.03 7.57 12/15/2008 8:25:59 AM Linearity Check 0 0 7.73 12/15/2008 8:26:29 AM Linearity Check 0 0 7.75 12/15/2008 8:26:59 AM Linearity Check 0 0 7.77 12/15/2008 8:27:29 AM Linearity Check 0 0 7.88 12/15/2008 8:27:59 AM Linearity Check 0 0 7.94 12/15/2008 8:28:29 AM Linearity Check 0 0 7.99 12/15/2008 8:28:59 AM Linearity Check 0 0 7.99 12/15/2008 8:29:29 AM Linearity Check 0 -0.01 7.97 12/15/2008 8:29:59 AM Linearity Check 0 -0.01 7.97 12/15/2008 8:30:29 AM Linearity Check 0 0 4.55 12/15/2008 8:30:59 AM Linearity Check 0 -0.01 4.08 12/15/2008 8:31:29 AM Linearity Check 0 -0.01 4.07 12/15/2008 8:31:59 AM Linearity Check 0 -0.01 3.96 12/15/2008 8:32:29 AM Linearity Check 0.01 -0.01 2.3 12/15/2008 8:32:59 AM Linearity Check 20.16 0.05 0.8 12/15/2008 8:33:29 AM Linearity Check 19.21 0.06 0.46 12/15/2008 8:33:59 AM Linearity Check 20.99 0 0.28 12/15/2008 8:34:29 AM Linearity Check 21 -0.01 0.29 12/15/2008 8:34:59 AM - ZERO 21 -0.01 0.29 12/15/2008 8:35:29 AM - ZERO 20.99 -0.01 0.34 12/15/2008 8:35:59 AM - ZERO 20.99 -0.01 -0.03 12/15/2008 8:36:29 AM - ZERO 20.98 -0.01 -0.02 12/15/2008 8:36:59 AM - ZERO 20.98 -0.01 0 12/15/2008 8:37:29 AM - ZERO 20.97 -0.01 -0.01 12/15/2008 8:37:59 AM - ZERO 20.87 0 -0.24 12/15/2008 8:38:29 AM - ZERO 11.25 7.39 -0.31 12/15/2008 8:38:59 AM - ZERO 10.61 8.77 -0.3 12/15/2008 8:39:29 AM - Span 10.58 8.83 -0.28 12/15/2008 8:39:59 AM - Span 10.57 8.85 -0.29 12/15/2008 8:40:29 AM - Span 10.56 8.86 -0.29 12/15/2008 8:40:59 AM - Span 10.64 9.01 -0.27 12/15/2008 8:41:29 AM - Span 10.76 9.01 -0.29 12/15/2008 8:41:59 AM - Span 10.61 9.01 -0.29 12/15/2008 8:42:29 AM - Span 10.67 9.01 0.17 12/15/2008 8:42:59 AM - Span 4.19 4.01 2.66 12/15/2008 8:43:29 AM - Span 0.3 0.19 3.86 12/15/2008 8:43:59 AM - Span 0.26 0.07 3.9 12/15/2008 8:44:29 AM - ZERO 0.18 0.04 3.87 12/15/2008 8:44:59 AM - ZERO 0.13 0.03 3.9 12/15/2008 8:45:29 AM - Span 0.15 0.02 3.91 12/15/2008 8:45:59 AM - ZERO 0.07 0.02 3.89 12/15/2008 8:46:29 AM - ZERO 0.03 0.01 3.93

Page 2 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 8:46:59 AM - ZERO 0.17 0.01 3.89 12/15/2008 8:47:29 AM - ZERO 6.27 0.01 1.13 12/15/2008 8:47:59 AM - ZERO 20.3 0.05 0.12 12/15/2008 8:48:29 AM - ZERO 20.72 0.07 0.16 12/15/2008 8:48:59 AM - ZERO 20.72 0.06 0.11 12/15/2008 8:49:29 AM - ZERO 20.29 0.06 0.13 12/15/2008 8:49:59 AM - ZERO 20.76 0.05 0.13 12/15/2008 8:50:29 AM - ZERO 20.94 0.06 0.1 12/15/2008 8:50:59 AM - ZERO 20.95 0.06 0.12 12/15/2008 8:51:29 AM - ZERO 20.94 0.06 0.12 12/15/2008 8:51:59 AM - ZERO 20.93 0.07 0.11 12/15/2008 8:52:29 AM - ZERO 20.77 0.07 0.14 12/15/2008 8:52:59 AM - ZERO 20.97 0.05 0.08 12/15/2008 8:53:29 AM - ZERO 20.95 0.05 0.13 12/15/2008 8:53:59 AM - ZERO 20.93 0.08 0.11 12/15/2008 8:54:29 AM - ZERO 20.93 0.08 0.12 12/15/2008 8:54:59 AM - ZERO 20.93 0.08 0.14 12/15/2008 8:55:29 AM - ZERO 20.95 0.06 0.12 12/15/2008 8:55:59 AM - ZERO 20.97 0.05 0.1 12/15/2008 8:56:29 AM - ZERO 20.98 0.04 0.12 12/15/2008 8:56:59 AM - ZERO 20.94 0.07 0.13 12/15/2008 8:57:29 AM - ZERO 20.96 0.06 0.11 12/15/2008 8:57:59 AM - ZERO 20.96 0.07 0.15 12/15/2008 8:58:29 AM - ZERO 20.97 0.05 0.14 12/15/2008 8:58:59 AM - ZERO 20.74 0.08 2.81 12/15/2008 8:59:29 AM - ZERO 12.27 7.87 5.55 12/15/2008 8:59:59 AM - ZERO 11.91 8.89 5.64 12/15/2008 9:00:29 AM - ZERO 11.87 8.91 5.72 12/15/2008 9:00:59 AM - ZERO 11.87 8.93 5.56 12/15/2008 9:01:29 AM - ZERO 11.88 8.94 5.4 12/15/2008 9:01:59 AM - ZERO 11.89 8.94 5.44 12/15/2008 9:02:29 AM - ZERO 12.41 8.94 5.49 12/15/2008 9:02:59 AM - ZERO 12.41 8.95 5.51 12/15/2008 9:03:29 AM - ZERO 12.24 8.97 5.54 12/15/2008 9:03:59 AM - ZERO 12.14 8.98 5.56 12/15/2008 9:04:29 AM - ZERO 12.12 8.98 5.51 12/15/2008 9:04:59 AM - ZERO 12.13 8.97 5.66 12/15/2008 9:05:29 AM - ZERO 12.41 8.97 5.59 12/15/2008 9:05:59 AM - ZERO 12.32 8.99 5.04 12/15/2008 9:25:29 AM TRAVERSE1 - 1 11.91 8.98 5.41 12/15/2008 9:25:59 AM TRAVERSE1 - 1 11.91 8.96 5.42 12/15/2008 9:26:29 AM TRAVERSE1 - 1 11.92 8.98 5.49 12/15/2008 9:26:59 AM TRAVERSE1 - 1 11.91 8.97 5.51 12/15/2008 9:27:29 AM TRAVERSE1 - 1 11.9 8.98 5.37 12/15/2008 9:27:59 AM TRAVERSE1 - 1 11.93 8.96 5.36 12/15/2008 9:28:29 AM TRAVERSE1 - 1 11.91 8.96 5.41 12/15/2008 9:28:59 AM TRAVERSE1 - 1 11.91 8.94 5.62 12/15/2008 9:29:29 AM TRAVERSE1 - 1 11.9 8.96 5.64 12/15/2008 9:29:59 AM TRAVERSE1 - 1 11.91 8.97 5.33 12/15/2008 9:30:29 AM TRAVERSE1 - 1 11.95 8.93 5.36 12/15/2008 9:30:59 AM TRAVERSE1 - 1 12.01 8.94 5.27 12/15/2008 9:31:29 AM TRAVERSE1 - 1 12.1 8.94 5.15 12/15/2008 9:31:59 AM TRAVERSE1 - 1 12.12 8.94 5.21 12/15/2008 9:32:29 AM TRAVERSE1 - 1 12.15 8.95 5.29

Page 3 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 9:32:59 AM TRAVERSE1 - 1 12.17 8.95 5.63 12/15/2008 9:33:29 AM TRAVERSE1 - 1 12.17 8.95 5.45 12/15/2008 9:33:59 AM TRAVERSE1 - 1 11.91 8.93 5.45 12/15/2008 9:34:29 AM TRAVERSE1 - 1 12 8.93 5.56 12/15/2008 9:34:59 AM TRAVERSE1 - 1 11.93 8.95 5.51 12/15/2008 9:35:29 AM TRAVERSE1 - 1 11.99 8.94 5.49 12/15/2008 9:35:59 AM TRAVERSE1 - 1 12.01 8.96 5.36 12/15/2008 9:36:29 AM TRAVERSE1 - 1 12.01 8.94 5.2 12/15/2008 9:36:59 AM TRAVERSE1 - 1 11.99 8.92 5.16 5.402083333 12/15/2008 9:37:29 AM Run Paused 11.92 8.92 5.6 12/15/2008 9:37:59 AM Run Paused 11.87 8.95 5.66 12/15/2008 9:38:29 AM Run Paused 13.45 8.02 4.61 12/15/2008 9:38:59 AM Run Paused 12.17 8.32 5.4 12/15/2008 9:39:29 AM Run Paused 11.94 8.91 5.56 12/15/2008 9:39:59 AM Run Paused 11.97 8.94 5.52 12/15/2008 9:40:29 AM TRAVERSE1 - 1 11.96 8.94 5.56 12/15/2008 9:40:59 AM TRAVERSE1 - 1 11.96 8.92 5.46 12/15/2008 9:41:29 AM TRAVERSE1 - 1 11.96 8.91 5.42 12/15/2008 9:41:59 AM TRAVERSE1 - 1 11.99 8.92 5.45 12/15/2008 9:42:29 AM TRAVERSE1 - 1 11.98 8.92 5.25 12/15/2008 9:42:59 AM TRAVERSE1 - 1 11.99 8.92 5.3 12/15/2008 9:43:29 AM TRAVERSE1 - 1 12.13 8.91 5.28 12/15/2008 9:43:59 AM TRAVERSE1 - 1 12.26 8.93 5.34 12/15/2008 9:44:29 AM TRAVERSE1 - 1 12.37 8.92 5.45 12/15/2008 9:44:59 AM TRAVERSE1 - 1 12.37 8.92 5.39 12/15/2008 9:45:29 AM TRAVERSE1 - 1 12.28 8.92 5.53 12/15/2008 9:45:59 AM TRAVERSE1 - 1 12.15 8.93 5.55 12/15/2008 9:46:29 AM TRAVERSE1 - 1 12.06 8.93 5.49 12/15/2008 9:46:59 AM TRAVERSE1 - 1 12 8.92 5.2 12/15/2008 9:47:29 AM TRAVERSE1 - 1 12.26 8.9 5.04 12/15/2008 9:47:59 AM TRAVERSE1 - 1 12.13 8.9 5.27 12/15/2008 9:48:29 AM TRAVERSE1 - 1 12.33 8.92 5.56 12/15/2008 9:48:59 AM TRAVERSE1 - 1 11.97 8.92 5.41 12/15/2008 9:49:29 AM TRAVERSE1 - 1 12.1 8.91 5.33 12/15/2008 9:49:59 AM TRAVERSE1 - 1 12.01 8.91 5.61 12/15/2008 9:50:29 AM TRAVERSE1 - 1 12.16 8.92 5.47 12/15/2008 9:50:59 AM TRAVERSE1 - 1 12.03 8.91 5.49 12/15/2008 9:51:29 AM TRAVERSE1 - 1 12.11 8.91 5.52 12/15/2008 9:51:59 AM TRAVERSE1 - 1 12.01 8.91 5.34 5.404583333 12/15/2008 9:52:29 AM Run Paused 11.99 8.9 5.37 12/15/2008 9:52:59 AM Run Paused 11.99 8.9 5.5 12/15/2008 9:53:29 AM Run Paused 11.95 8.89 5.78 12/15/2008 9:53:59 AM Run Paused 12.02 8.9 5.68 12/15/2008 9:54:29 AM Run Paused 12.09 8.89 5.71 12/15/2008 9:54:59 AM Run Paused 12.01 8.91 5.56 12/15/2008 9:55:29 AM Run Paused 12.73 8.7 4.26 12/15/2008 9:55:59 AM Run Paused 12.5 7.86 5.25 12/15/2008 9:56:29 AM Run Paused 12.21 8.87 5.45 12/15/2008 9:56:59 AM TRAVERSE1 - 1 12.01 8.88 5.49 12/15/2008 9:57:29 AM TRAVERSE1 - 1 12.15 8.89 5.48 12/15/2008 9:57:59 AM TRAVERSE1 - 1 12.02 8.89 5.92 12/15/2008 9:58:29 AM TRAVERSE1 - 1 11.97 8.92 5.79 12/15/2008 9:58:59 AM TRAVERSE1 - 1 11.93 8.89 5.78 12/15/2008 9:59:29 AM TRAVERSE1 - 1 12.11 8.93 5.63

Page 4 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 9:59:59 AM TRAVERSE1 - 1 11.98 8.89 5.52 12/15/2008 10:00:29 AM TRAVERSE1 - 1 12.12 8.88 5.53 12/15/2008 10:00:59 AM TRAVERSE1 - 1 12.38 8.9 5.45 12/15/2008 10:01:29 AM TRAVERSE1 - 1 12.38 8.88 5.45 12/15/2008 10:01:59 AM TRAVERSE1 - 1 12.23 8.9 5.23 12/15/2008 10:02:29 AM TRAVERSE1 - 1 12.12 8.88 5.26 12/15/2008 10:02:59 AM TRAVERSE1 - 1 12.12 8.88 5.39 12/15/2008 10:03:29 AM TRAVERSE1 - 1 12.05 8.89 5.4 12/15/2008 10:03:59 AM TRAVERSE1 - 1 12.04 8.89 5.42 12/15/2008 10:04:29 AM TRAVERSE1 - 1 12.05 8.89 5.33 12/15/2008 10:04:59 AM TRAVERSE1 - 1 12.04 8.88 5.38 12/15/2008 10:05:29 AM TRAVERSE1 - 1 12.15 8.89 5.22 12/15/2008 10:05:59 AM TRAVERSE1 - 1 12.15 8.9 4.99 12/15/2008 10:06:29 AM TRAVERSE1 - 1 12.17 8.92 4.6 12/15/2008 10:06:59 AM TRAVERSE1 - 1 12.17 8.92 5.16 12/15/2008 10:07:29 AM TRAVERSE1 - 1 12.16 8.88 5.33 12/15/2008 10:07:59 AM TRAVERSE1 - 1 12.14 8.9 5.42 12/15/2008 10:08:29 AM TRAVERSE1 - 1 12.11 8.9 5.16 5.38875 12/15/2008 10:08:59 AM Run Paused 12.14 8.88 5.03 12/15/2008 10:09:29 AM Run Paused 12.14 8.87 5.14 12/15/2008 10:09:59 AM Run Paused 12.16 8.89 4.97 12/15/2008 10:10:29 AM Run Paused 16.18 5.42 0.62 12/15/2008 10:10:59 AM Run Paused 18.37 2.1 4.21 12/15/2008 10:11:29 AM Run Paused 12.25 8.35 5.21 12/15/2008 10:11:59 AM Run Paused 12.22 8.85 5.27 12/15/2008 10:12:29 AM TRAVERSE1 - 1 12.06 8.88 5.18 12/15/2008 10:12:59 AM TRAVERSE1 - 1 12.32 8.88 4.95 12/15/2008 10:13:29 AM TRAVERSE1 - 1 12.41 8.88 4.98 12/15/2008 10:13:59 AM TRAVERSE1 - 1 12.4 8.87 4.96 12/15/2008 10:14:29 AM TRAVERSE1 - 1 12.41 8.86 5.28 12/15/2008 10:14:59 AM TRAVERSE1 - 1 12.38 8.88 5.36 12/15/2008 10:15:29 AM TRAVERSE1 - 1 12.16 8.89 5.16 12/15/2008 10:15:59 AM TRAVERSE1 - 1 12.14 8.87 5.14 12/15/2008 10:16:29 AM TRAVERSE1 - 1 12.19 8.88 5.25 12/15/2008 10:16:59 AM TRAVERSE1 - 1 12.34 8.89 4.98 12/15/2008 10:17:29 AM TRAVERSE1 - 1 12.16 8.87 5.04 12/15/2008 10:17:59 AM TRAVERSE1 - 1 12.41 8.87 5.05 12/15/2008 10:18:29 AM TRAVERSE1 - 1 12.41 8.87 5.23 12/15/2008 10:18:59 AM TRAVERSE1 - 1 12.39 8.87 5.41 12/15/2008 10:19:29 AM TRAVERSE1 - 1 12.39 8.88 5.32 12/15/2008 10:19:59 AM TRAVERSE1 - 1 12.39 8.88 5.21 12/15/2008 10:20:29 AM TRAVERSE1 - 1 12.39 8.89 5.14 12/15/2008 10:20:59 AM TRAVERSE1 - 1 12.39 8.86 4.96 12/15/2008 10:21:29 AM TRAVERSE1 - 1 12.41 8.88 4.78 12/15/2008 10:21:59 AM TRAVERSE1 - 1 12.41 8.86 4.96 12/15/2008 10:22:29 AM TRAVERSE1 - 1 12.36 8.86 5.19 12/15/2008 10:22:59 AM TRAVERSE1 - 1 12.36 8.88 5.12 12/15/2008 10:23:29 AM TRAVERSE1 - 1 12.38 8.87 5.03 12/15/2008 10:23:59 AM TRAVERSE1 - 1 12.37 8.86 4.99 5.11125 12/15/2008 10:24:29 AM 12.36 8.86 5.01 12/15/2008 10:24:59 AM 12.36 8.85 5.13 12/15/2008 10:25:29 AM 6.6 4.89 7.54 12/15/2008 10:25:59 AM 0.43 0.34 4.35 12/15/2008 10:26:29 AM - Span 0.25 0.07 4.36

Page 5 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 10:26:59 AM - Span 0.28 0.04 4.34 12/15/2008 10:27:29 AM - Span 0.18 0.03 3.97 12/15/2008 10:27:59 AM - Span 0.03 0.03 4 12/15/2008 10:28:29 AM - ZERO 0.03 0.02 3.96 12/15/2008 10:28:59 AM - ZERO 3.21 2.1 1.32 12/15/2008 10:29:29 AM - Span 10.19 7.91 0.2 12/15/2008 10:29:59 AM - Span 10.61 8.83 0.17 12/15/2008 10:30:29 AM - Span 10.52 8.87 0.16 12/15/2008 10:30:59 AM - Span 10.69 8.88 0.17 12/15/2008 10:31:29 AM - ZERO 10.69 8.89 0.16 12/15/2008 10:31:59 AM - ZERO 10.53 8.9 0.16 12/15/2008 10:32:29 AM - ZERO 10.54 8.9 0.22 12/15/2008 10:32:59 AM - ZERO 18.64 2.88 0.41 12/15/2008 10:33:29 AM - ZERO 20.87 0.17 0.47 12/15/2008 10:33:59 AM - ZERO 20.9 0.07 0.47 12/15/2008 10:34:29 AM - ZERO 20.91 0.05 -0.01 12/15/2008 10:34:59 AM - ZERO 20.92 0.03 0.01 12/15/2008 10:35:29 AM - ZERO 20.93 0.03 0 12/15/2008 10:35:59 AM - ZERO 20.88 0.02 1.47 12/15/2008 10:36:29 AM - ZERO 0.71 0.02 3.46 12/15/2008 10:36:59 AM - ZERO 0.11 0.01 3.45 12/15/2008 10:37:29 AM - ZERO 0.07 0.01 3.95 12/15/2008 10:37:59 AM - ZERO 0.05 0.01 4.01 12/15/2008 10:38:29 AM - ZERO 0.04 0.01 3.97 12/15/2008 10:38:59 AM - ZERO 4.94 3.02 4.53 12/15/2008 10:39:29 AM - ZERO 11.74 8.18 4.77 12/15/2008 10:39:59 AM - ZERO 12.26 8.81 4.51 12/15/2008 10:40:29 AM - ZERO 12.13 8.84 4.61 12/15/2008 10:40:59 AM - ZERO 12.08 8.85 4.65 12/15/2008 10:41:29 AM - ZERO 9.18 7.45 3.68 12/15/2008 10:41:59 AM - ZERO 0.16 0.58 3.18 12/15/2008 10:42:29 AM - ZERO 0 0.01 3.2 12/15/2008 10:42:59 AM - ZERO 0 0 3.99 12/15/2008 10:43:29 AM - ZERO 8.58 4.85 5.32 12/15/2008 10:43:59 AM - ZERO 4.49 3.83 5.15 12/15/2008 10:44:29 AM - ZERO 0.42 0.16 4.95 12/15/2008 10:44:59 AM - ZERO 0.34 0.04 4.97 12/15/2008 10:45:29 AM - ZERO 0.03 0.03 4.97 12/15/2008 10:45:59 AM - ZERO 0.03 0.02 4.96 12/15/2008 10:46:29 AM - ZERO 2.77 1.45 5.23 12/15/2008 10:46:59 AM - ZERO 11.49 7.73 5.71 12/15/2008 10:47:29 AM - ZERO 11.95 8.79 5.73 12/15/2008 10:47:59 AM - ZERO 8.95 7.38 5.54 12/15/2008 10:48:29 AM - ZERO 0.34 0.76 5 12/15/2008 10:48:59 AM - ZERO 0.05 0.05 4.99 12/15/2008 10:49:29 AM - ZERO 0.03 0.03 4.99 12/15/2008 10:49:59 AM - ZERO 0.02 0.02 3.98 12/15/2008 10:50:29 AM - ZERO 0.03 0.01 3.96 12/15/2008 10:50:59 AM - ZERO 7.09 4.5 4.47 12/15/2008 10:51:29 AM - ZERO 11.89 8.49 4.4 12/15/2008 10:51:59 AM - ZERO 11.99 8.78 4.38 12/15/2008 10:52:29 AM - ZERO 11.99 8.79 4.5 12/15/2008 10:52:59 AM - ZERO 11.96 8.81 4.7 12/15/2008 10:53:29 AM - ZERO 11.95 8.82 4.66

Page 6 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 10:53:59 AM - ZERO 11.97 8.81 4.61 12/15/2008 10:54:29 AM - ZERO 11.98 8.82 4.96 12/15/2008 10:54:59 AM - ZERO 11.98 8.82 4.95 12/15/2008 10:55:29 AM - ZERO 11.99 8.81 5.17 12/15/2008 10:55:59 AM - ZERO 12.02 8.81 5.06 12/15/2008 10:56:29 AM RUN 1 - 1 12.02 8.82 5.12 12/15/2008 10:56:59 AM RUN 1 - 1 12.02 8.81 5.16 12/15/2008 10:57:29 AM RUN 1 - 1 11.99 8.82 5.33 12/15/2008 10:57:59 AM RUN 1 - 1 12.2 8.83 5.32 12/15/2008 10:58:29 AM RUN 1 - 1 11.97 8.82 5.43 12/15/2008 10:58:59 AM RUN 1 - 1 12.13 8.83 5.4 12/15/2008 10:59:29 AM RUN 1 - 1 12.43 8.83 5.25 12/15/2008 10:59:59 AM RUN 1 - 1 12 8.82 5.21 12/15/2008 11:00:29 AM RUN 1 - 1 12 8.82 5.32 12/15/2008 11:00:59 AM RUN 1 - 1 12 8.84 5.27 12/15/2008 11:01:29 AM RUN 1 - 1 12 8.83 5.1 12/15/2008 11:01:59 AM RUN 1 - 1 12.02 8.81 5.14 12/15/2008 11:02:29 AM RUN 1 - 1 12.02 8.81 5.15 12/15/2008 11:02:59 AM RUN 1 - 1 12.02 8.82 5.08 12/15/2008 11:03:29 AM RUN 1 - 1 12.05 8.81 5.09 12/15/2008 11:03:59 AM RUN 1 - 1 12.01 8.82 5.26 12/15/2008 11:04:29 AM RUN 1 - 1 12.01 8.82 5.29 12/15/2008 11:04:59 AM RUN 1 - 1 11.99 8.81 5.44 12/15/2008 11:05:29 AM RUN 1 - 1 12 8.81 5.34 12/15/2008 11:05:59 AM RUN 1 - 1 12 8.81 5.33 12/15/2008 11:06:29 AM RUN 1 - 1 12.02 8.81 5 12/15/2008 11:06:59 AM RUN 1 - 1 12.02 8.83 4.43 12/15/2008 11:07:29 AM RUN 1 - 1 12.02 8.83 5.23 12/15/2008 11:07:59 AM RUN 1 - 1 12.01 8.82 5.35 12/15/2008 11:08:29 AM RUN 1 - 1 11.97 8.81 5.49 12/15/2008 11:08:59 AM RUN 1 - 1 11.96 8.82 5.49 12/15/2008 11:09:29 AM RUN 1 - 1 11.98 8.81 5.42 12/15/2008 11:09:59 AM RUN 1 - 1 11.98 8.81 5.37 12/15/2008 11:10:29 AM RUN 1 - 1 11.99 8.81 5.12 12/15/2008 11:10:59 AM RUN 1 - 1 12 8.8 5.29 12/15/2008 11:11:29 AM RUN 1 - 1 11.96 8.83 5.36 12/15/2008 11:11:59 AM RUN 1 - 1 11.96 8.81 5.49 12/15/2008 11:12:29 AM RUN 1 - 1 11.94 8.8 5.69 12/15/2008 11:12:59 AM RUN 1 - 1 11.94 8.82 5.52 12/15/2008 11:13:29 AM RUN 1 - 1 11.95 8.81 5.49 12/15/2008 11:13:59 AM RUN 1 - 1 11.96 8.81 5.17 12/15/2008 11:14:29 AM RUN 1 - 1 12.07 8.8 5.25 12/15/2008 11:14:59 AM RUN 1 - 1 12.06 8.81 5.33 12/15/2008 11:15:29 AM RUN 1 - 1 11.91 8.82 5.49 12/15/2008 11:15:59 AM RUN 1 - 1 12.06 8.82 5.48 12/15/2008 11:16:29 AM RUN 1 - 1 12.06 8.82 5.5 12/15/2008 11:16:59 AM RUN 1 - 1 12.01 8.83 5.51 12/15/2008 11:17:29 AM RUN 1 - 1 12.23 8.81 5.31 12/15/2008 11:17:59 AM RUN 1 - 1 12.16 8.8 5.69 12/15/2008 11:18:29 AM RUN 1 - 1 12.1 8.81 5.59 12/15/2008 11:18:59 AM RUN 1 - 1 12.35 8.81 5.66 12/15/2008 11:19:29 AM RUN 1 - 1 12.19 8.82 5.47 12/15/2008 11:19:59 AM RUN 1 - 1 12.13 8.81 5.51 12/15/2008 11:20:29 AM RUN 1 - 1 12.35 8.82 5.48

Page 7 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 11:20:59 AM RUN 1 - 1 12.12 8.82 5.24 12/15/2008 11:21:29 AM RUN 1 - 1 12.11 8.8 5.14 12/15/2008 11:21:59 AM RUN 1 - 1 12.18 8.8 5.17 12/15/2008 11:22:29 AM RUN 1 - 1 12.17 8.8 5.04 12/15/2008 11:22:59 AM RUN 1 - 1 12.19 8.79 5.11 12/15/2008 11:23:29 AM RUN 1 - 1 12.21 8.79 5.2 12/15/2008 11:23:59 AM RUN 1 - 1 12.12 8.8 5.21 12/15/2008 11:24:29 AM RUN 1 - 1 12.17 8.78 5.25 12/15/2008 11:24:59 AM RUN 1 - 1 12.23 8.81 5.19 12/15/2008 11:25:29 AM RUN 1 - 1 12.22 8.81 5.15 12/15/2008 11:25:59 AM RUN 1 - 1 12.24 8.78 5.27 12/15/2008 11:26:29 AM RUN 1 - 1 12.26 8.79 5.28 12/15/2008 11:26:59 AM RUN 1 - 1 12.24 8.8 5.07 12/15/2008 11:27:29 AM RUN 1 - 1 12.27 8.78 5.18 12/15/2008 11:27:59 AM RUN 1 - 1 12.11 8.78 5.3 12/15/2008 11:28:29 AM RUN 1 - 1 12.12 8.78 5.46 12/15/2008 11:28:59 AM RUN 1 - 1 12.17 8.79 5.36 12/15/2008 11:29:29 AM RUN 1 - 1 12.11 8.8 5.34 12/15/2008 11:29:59 AM RUN 1 - 1 12.13 8.79 5.15 12/15/2008 11:30:29 AM RUN 1 - 1 12.12 8.8 5.22 12/15/2008 11:30:59 AM RUN 1 - 1 12.17 8.8 5.25 12/15/2008 11:31:29 AM RUN 1 - 1 12.16 8.81 5.22 12/15/2008 11:31:59 AM RUN 1 - 1 12.16 8.8 5.39 12/15/2008 11:32:29 AM RUN 1 - 1 12.2 8.82 5.37 12/15/2008 11:32:59 AM RUN 1 - 1 12.19 8.81 5.3 12/15/2008 11:33:29 AM RUN 1 - 1 12.18 8.79 5.45 12/15/2008 11:33:59 AM RUN 1 - 1 12.19 8.8 5.43 12/15/2008 11:34:29 AM RUN 1 - 1 12.16 8.79 5.39 12/15/2008 11:34:59 AM RUN 1 - 1 12.16 8.81 5.41 12/15/2008 11:35:29 AM RUN 1 - 1 12.22 8.81 5.45 12/15/2008 11:35:59 AM RUN 1 - 1 12.22 8.83 5.27 12/15/2008 11:36:29 AM RUN 1 - 1 12.22 8.81 5.39 12/15/2008 11:36:59 AM RUN 1 - 1 12.19 8.81 5.18 12/15/2008 11:37:29 AM RUN 1 - 1 12.2 8.8 5.41 12/15/2008 11:37:59 AM RUN 1 - 1 12.15 8.79 5.5 12/15/2008 11:38:29 AM RUN 1 - 1 12.17 8.8 5.45 12/15/2008 11:38:59 AM RUN 1 - 1 12.19 8.8 5.51 12/15/2008 11:39:29 AM RUN 1 - 1 12.13 8.8 5.54 12/15/2008 11:39:59 AM RUN 1 - 1 12.23 8.8 5.5 12/15/2008 11:40:29 AM RUN 1 - 1 12.29 8.8 5.21 12/15/2008 11:40:59 AM RUN 1 - 1 12.19 8.79 5.12 12/15/2008 11:41:29 AM RUN 1 - 1 12.16 8.79 5.3 12/15/2008 11:41:59 AM RUN 1 - 1 12.15 8.8 5.46 12/15/2008 11:42:29 AM RUN 1 - 1 12.13 8.81 5.45 12/15/2008 11:42:59 AM RUN 1 - 1 12.15 8.82 5.47 12/15/2008 11:43:29 AM RUN 1 - 1 12.15 8.8 5.48 12/15/2008 11:43:59 AM RUN 1 - 1 12.16 8.82 5.26 12/15/2008 11:44:29 AM RUN 1 - 1 12.19 8.8 5.19 12/15/2008 11:44:59 AM RUN 1 - 1 12.17 8.8 5.3 12/15/2008 11:45:29 AM RUN 1 - 1 12.16 8.81 5.47 12/15/2008 11:45:59 AM RUN 1 - 1 12.13 8.82 5.37 12/15/2008 11:46:29 AM RUN 1 - 1 12.16 8.8 5.55 12/15/2008 11:46:59 AM RUN 1 - 1 12.18 8.83 5.52 12/15/2008 11:47:29 AM RUN 1 - 1 12.16 8.81 5.62

Page 8 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 11:47:59 AM RUN 1 - 1 12.17 8.82 5.45 12/15/2008 11:48:29 AM RUN 1 - 1 12.2 8.81 5.32 12/15/2008 11:48:59 AM RUN 1 - 1 12.23 8.8 5.36 12/15/2008 11:49:29 AM RUN 1 - 1 12.22 8.8 5.33 12/15/2008 11:49:59 AM RUN 1 - 1 12.22 8.8 5.27 12/15/2008 11:50:29 AM RUN 1 - 1 12.21 8.81 5.32 12/15/2008 11:50:59 AM RUN 1 - 1 12.23 8.8 5.49 12/15/2008 11:51:29 AM RUN 1 - 1 12.22 8.81 5.46 12/15/2008 11:51:59 AM RUN 1 - 1 12.23 8.8 5.37 12/15/2008 11:52:29 AM RUN 1 - 1 12.25 8.81 5.33 12/15/2008 11:52:59 AM RUN 1 - 1 12.24 8.81 5.29 12/15/2008 11:53:29 AM RUN 1 - 1 12.26 8.8 5.18 12/15/2008 11:53:59 AM RUN 1 - 1 12.25 8.81 5.32 12/15/2008 11:54:29 AM RUN 1 - 1 12.23 8.8 5.53 12/15/2008 11:54:59 AM RUN 1 - 1 12.21 8.81 5.37 12/15/2008 11:55:29 AM RUN 1 - 1 12.22 8.79 5.32 12/15/2008 11:55:59 AM RUN 1 - 1 12.22 8.79 5.31 12/15/2008 11:56:29 AM 12.21 8.79 5.31 12/15/2008 11:56:59 AM 12.23 8.8 8.05 12/15/2008 11:57:29 AM 4.55 3.24 9.55 12/15/2008 11:57:59 AM 0.46 0.17 4.87 12/15/2008 11:58:29 AM 0.35 0.06 4.89 12/15/2008 11:58:59 AM 0.23 0.04 4.86 12/15/2008 11:59:29 AM 0.24 0.03 4.86 12/15/2008 11:59:59 AM - ZERO 0.25 0.02 4.86 12/15/2008 12:00:29 PM - ZERO 0.21 0.02 3.82 12/15/2008 12:00:59 PM - Span 0.21 0.02 3.96 12/15/2008 12:01:29 PM - Span 0.21 0.02 3.98 12/15/2008 12:01:59 PM - ZERO 0.16 0.01 3.88 12/15/2008 12:02:29 PM - ZERO 5.98 4.29 0.59 12/15/2008 12:02:59 PM - ZERO 10.51 8.49 0.02 12/15/2008 12:03:29 PM - Span 10.59 8.82 -0.02 12/15/2008 12:03:59 PM - ZERO 10.6 8.84 -0.01 12/15/2008 12:04:29 PM - ZERO 10.52 8.86 -0.01 12/15/2008 12:04:59 PM - ZERO 10.51 8.87 1.03 12/15/2008 12:05:29 PM - ZERO 11.8 8.83 4.28 12/15/2008 12:05:59 PM - ZERO 11.99 8.83 4.32 12/15/2008 12:06:29 PM - ZERO 12.02 8.81 4.29 12/15/2008 12:06:59 PM - ZERO 12 8.8 5.06 12/15/2008 12:07:29 PM - ZERO 11.95 8.82 4.83 12/15/2008 12:07:59 PM - ZERO 11.9 8.85 5.69 12/15/2008 12:08:29 PM - ZERO 11.93 8.82 5.69 12/15/2008 12:08:59 PM - ZERO 11.92 8.81 5.55 12/15/2008 12:09:29 PM - ZERO 11.97 8.8 5.14 12/15/2008 12:09:59 PM - ZERO 11.98 8.79 4.66 12/15/2008 12:10:29 PM - ZERO 3.21 3.48 4.66 12/15/2008 12:10:59 PM - ZERO 0.08 0.17 4.78 12/15/2008 12:11:29 PM - ZERO 0.05 0.07 4.8 12/15/2008 12:11:59 PM - ZERO 0.04 0.05 3.99 12/15/2008 12:12:29 PM - ZERO 0.03 0.04 4 12/15/2008 12:12:59 PM - ZERO 4.36 2.7 4.22 12/15/2008 12:13:29 PM - ZERO 11.63 7.96 4.54 12/15/2008 12:13:59 PM - ZERO 11.94 8.75 4.96 12/15/2008 12:14:29 PM - ZERO 11.96 8.77 5.03

Page 9 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 12:14:59 PM - ZERO 11.96 8.79 5.01 12/15/2008 12:15:29 PM - ZERO 11.99 8.78 4.99 12/15/2008 12:15:59 PM - ZERO 12 8.78 4.89 12/15/2008 12:16:29 PM - ZERO 11.99 8.79 4.9 12/15/2008 12:16:59 PM RUN 2 - 1 11.96 8.8 5.14 12/15/2008 12:17:29 PM RUN 2 - 1 11.97 8.8 5.08 12/15/2008 12:17:59 PM RUN 2 - 1 11.96 8.78 5.08 12/15/2008 12:18:29 PM RUN 2 - 1 11.96 8.8 5.09 12/15/2008 12:18:59 PM RUN 2 - 1 11.95 8.79 5.22 12/15/2008 12:19:29 PM RUN 2 - 1 11.95 8.8 5.27 12/15/2008 12:19:59 PM RUN 2 - 1 12.01 8.79 5.25 12/15/2008 12:20:29 PM RUN 2 - 1 11.98 8.8 5.1 12/15/2008 12:20:59 PM RUN 2 - 1 12.04 8.78 5.05 12/15/2008 12:21:29 PM RUN 2 - 1 12.06 8.8 5.01 12/15/2008 12:21:59 PM RUN 2 - 1 12.04 8.81 4.82 12/15/2008 12:22:29 PM RUN 2 - 1 12.01 8.8 5.08 12/15/2008 12:22:59 PM RUN 2 - 1 11.97 8.8 5.26 12/15/2008 12:23:29 PM RUN 2 - 1 12.04 8.79 5.27 12/15/2008 12:23:59 PM RUN 2 - 1 11.99 8.81 5.15 12/15/2008 12:24:29 PM RUN 2 - 1 11.98 8.79 5.19 12/15/2008 12:24:59 PM RUN 2 - 1 12.01 8.79 5.16 12/15/2008 12:25:29 PM RUN 2 - 1 12 8.8 5.11 12/15/2008 12:25:59 PM RUN 2 - 1 12.03 8.79 5.01 12/15/2008 12:26:29 PM RUN 2 - 1 12.02 8.79 5.15 12/15/2008 12:26:59 PM RUN 2 - 1 11.99 8.79 5.33 12/15/2008 12:27:29 PM RUN 2 - 1 11.95 8.81 5.23 12/15/2008 12:27:59 PM RUN 2 - 1 11.99 8.78 5.31 12/15/2008 12:28:29 PM RUN 2 - 1 11.94 8.79 5.34 12/15/2008 12:28:59 PM RUN 2 - 1 11.96 8.78 5.32 12/15/2008 12:29:29 PM RUN 2 - 1 11.96 8.78 5.19 12/15/2008 12:29:59 PM RUN 2 - 1 11.98 8.77 5.15 12/15/2008 12:30:29 PM RUN 2 - 1 11.97 8.79 5.36 12/15/2008 12:30:59 PM RUN 2 - 1 11.97 8.79 5.39 12/15/2008 12:31:29 PM RUN 2 - 1 11.91 8.79 5.53 12/15/2008 12:31:59 PM RUN 2 - 1 11.92 8.8 5.59 12/15/2008 12:32:29 PM RUN 2 - 1 11.91 8.81 5.56 12/15/2008 12:32:59 PM RUN 2 - 1 11.94 8.79 5.51 12/15/2008 12:33:29 PM RUN 2 - 1 11.94 8.8 5.47 12/15/2008 12:33:59 PM RUN 2 - 1 11.96 8.8 5.29 12/15/2008 12:34:29 PM RUN 2 - 1 11.98 8.79 5.26 12/15/2008 12:34:59 PM RUN 2 - 1 11.96 8.8 5.41 12/15/2008 12:35:29 PM RUN 2 - 1 11.97 8.8 5.26 12/15/2008 12:35:59 PM RUN 2 - 1 11.95 8.78 5.42 12/15/2008 12:36:29 PM RUN 2 - 1 11.92 8.8 5.33 12/15/2008 12:36:59 PM RUN 2 - 1 11.97 8.78 5.39 12/15/2008 12:37:29 PM RUN 2 - 1 11.96 8.79 5.45 12/15/2008 12:37:59 PM RUN 2 - 1 11.9 8.79 5.64 12/15/2008 12:38:29 PM RUN 2 - 1 11.9 8.8 5.52 12/15/2008 12:38:59 PM RUN 2 - 1 11.95 8.78 5.43 12/15/2008 12:39:29 PM RUN 2 - 1 11.94 8.81 5.41 12/15/2008 12:39:59 PM RUN 2 - 1 11.96 8.79 5.29 12/15/2008 12:40:29 PM RUN 2 - 1 11.97 8.79 5.23 12/15/2008 12:40:59 PM RUN 2 - 1 11.99 8.78 5.25 12/15/2008 12:41:29 PM RUN 2 - 1 12 8.79 5.3

Page 10 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 12:41:59 PM RUN 2 - 1 11.97 8.8 5.38 12/15/2008 12:42:29 PM RUN 2 - 1 12 8.8 5.22 12/15/2008 12:42:59 PM RUN 2 - 1 11.99 8.78 5.25 12/15/2008 12:43:29 PM RUN 2 - 1 11.97 8.79 5.34 12/15/2008 12:43:59 PM RUN 2 - 1 11.99 8.8 5.18 12/15/2008 12:44:29 PM RUN 2 - 1 12.02 8.79 5 12/15/2008 12:44:59 PM RUN 2 - 1 11.98 8.79 5.28 12/15/2008 12:45:29 PM RUN 2 - 1 11.98 8.78 5.1 12/15/2008 12:45:59 PM RUN 2 - 1 11.98 8.78 5.06 12/15/2008 12:46:29 PM RUN 2 - 1 11.99 8.77 5.14 12/15/2008 12:46:59 PM RUN 2 - 1 11.98 8.78 5.23 12/15/2008 12:47:29 PM RUN 2 - 1 11.98 8.78 5.25 12/15/2008 12:47:59 PM RUN 2 - 1 11.98 8.8 5.19 12/15/2008 12:48:29 PM RUN 2 - 1 11.98 8.8 5.09 12/15/2008 12:48:59 PM RUN 2 - 1 11.97 8.8 4.97 12/15/2008 12:49:29 PM RUN 2 - 1 11.96 8.79 5.17 12/15/2008 12:49:59 PM RUN 2 - 1 11.95 8.79 5.3 12/15/2008 12:50:29 PM RUN 2 - 1 11.95 8.79 5.31 12/15/2008 12:50:59 PM RUN 2 - 1 11.95 8.81 5.23 12/15/2008 12:51:29 PM RUN 2 - 1 11.96 8.79 5.23 12/15/2008 12:51:59 PM RUN 2 - 1 11.95 8.79 5.25 12/15/2008 12:52:29 PM RUN 2 - 1 11.95 8.79 5.19 12/15/2008 12:52:59 PM RUN 2 - 1 11.96 8.78 5.3 12/15/2008 12:53:29 PM RUN 2 - 1 11.98 8.79 5.25 12/15/2008 12:53:59 PM RUN 2 - 1 11.97 8.79 5.17 12/15/2008 12:54:29 PM RUN 2 - 1 12 8.79 4.91 12/15/2008 12:54:59 PM RUN 2 - 1 11.99 8.78 5.03 12/15/2008 12:55:29 PM RUN 2 - 1 11.98 8.78 5.25 12/15/2008 12:55:59 PM RUN 2 - 1 11.94 8.78 5.38 12/15/2008 12:56:29 PM RUN 2 - 1 11.94 8.8 5.27 12/15/2008 12:56:59 PM RUN 2 - 1 11.98 8.78 5.22 12/15/2008 12:57:29 PM RUN 2 - 1 11.96 8.79 5.3 12/15/2008 12:57:59 PM RUN 2 - 1 11.95 8.8 5.34 12/15/2008 12:58:29 PM RUN 2 - 1 11.95 8.8 5.2 12/15/2008 12:58:59 PM RUN 2 - 1 11.96 8.79 5.25 12/15/2008 12:59:29 PM RUN 2 - 1 11.95 8.79 5.34 12/15/2008 12:59:59 PM RUN 2 - 1 11.95 8.8 5.29 12/15/2008 1:00:29 PM RUN 2 - 1 11.95 8.8 5.34 12/15/2008 1:00:59 PM RUN 2 - 1 11.94 8.82 5.27 12/15/2008 1:01:29 PM RUN 2 - 1 11.97 8.81 5.19 12/15/2008 1:01:59 PM RUN 2 - 1 11.98 8.8 5.05 12/15/2008 1:02:29 PM RUN 2 - 1 12 8.79 4.95 12/15/2008 1:02:59 PM RUN 2 - 1 12.02 8.78 5.01 12/15/2008 1:03:29 PM RUN 2 - 1 11.99 8.79 5.09 12/15/2008 1:03:59 PM RUN 2 - 1 12 8.79 5.28 12/15/2008 1:04:29 PM RUN 2 - 1 11.97 8.82 5.24 12/15/2008 1:04:59 PM RUN 2 - 1 11.99 8.79 5.06 12/15/2008 1:05:29 PM RUN 2 - 1 12 8.79 5.25 12/15/2008 1:05:59 PM RUN 2 - 1 12.01 8.79 5.02 12/15/2008 1:06:29 PM RUN 2 - 1 12.02 8.78 4.85 12/15/2008 1:06:59 PM RUN 2 - 1 12.05 8.78 4.95 12/15/2008 1:07:29 PM RUN 2 - 1 12.05 8.79 4.97 12/15/2008 1:07:59 PM RUN 2 - 1 11.98 8.82 4.58 12/15/2008 1:08:29 PM RUN 2 - 1 11.96 8.81 5.27

Page 11 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 1:08:59 PM RUN 2 - 1 11.98 8.79 5.28 12/15/2008 1:09:29 PM RUN 2 - 1 11.99 8.8 5.27 12/15/2008 1:09:59 PM RUN 2 - 1 12 8.81 5.05 12/15/2008 1:10:29 PM RUN 2 - 1 12.03 8.8 5.01 12/15/2008 1:10:59 PM RUN 2 - 1 12.02 8.78 5.05 12/15/2008 1:11:29 PM RUN 2 - 1 12.01 8.8 5.11 12/15/2008 1:11:59 PM RUN 2 - 1 12.02 8.81 5.08 12/15/2008 1:12:29 PM RUN 2 - 1 12.01 8.79 5.26 12/15/2008 1:12:59 PM RUN 2 - 1 12 8.81 5.37 12/15/2008 1:13:29 PM RUN 2 - 1 11.98 8.81 5.29 12/15/2008 1:13:59 PM RUN 2 - 1 11.98 8.8 5.28 12/15/2008 1:14:29 PM RUN 2 - 1 11.99 8.81 5.18 12/15/2008 1:14:59 PM RUN 2 - 1 12 8.8 5.08 12/15/2008 1:15:29 PM RUN 2 - 1 12.03 8.81 5.12 12/15/2008 1:15:59 PM RUN 2 - 1 12.02 8.81 5.12 12/15/2008 1:16:29 PM RUN 2 - 1 12.01 8.8 5.15 12/15/2008 1:16:59 PM 11.95 8.82 5.37 12/15/2008 1:17:29 PM 11.91 8.83 10 12/15/2008 1:17:59 PM 1.45 1.58 7.01 12/15/2008 1:18:29 PM 0.13 0.11 4.67 12/15/2008 1:18:59 PM - Span 0.12 0.05 3.97 12/15/2008 1:19:29 PM - Span 0.11 0.04 3.94 12/15/2008 1:19:59 PM - ZERO 0.1 0.03 3.97 12/15/2008 1:20:29 PM - ZERO 0.03 0.02 3.95 12/15/2008 1:20:59 PM - ZERO 0.03 0.02 3.76 12/15/2008 1:21:29 PM - ZERO 7.1 5.05 0.53 12/15/2008 1:21:59 PM - ZERO 10.44 8.57 0.06 12/15/2008 1:22:29 PM - ZERO 10.49 8.8 0.07 12/15/2008 1:22:59 PM - Span 10.5 8.83 0.06 12/15/2008 1:23:29 PM - Span 10.5 8.84 0.05 12/15/2008 1:23:59 PM - ZERO 10.5 8.84 0.07 12/15/2008 1:24:29 PM - ZERO 10.51 8.85 0.05 12/15/2008 1:24:59 PM - ZERO 10.51 8.86 0.04 12/15/2008 1:25:29 PM - ZERO 15.87 5.24 0.3 12/15/2008 1:25:59 PM - ZERO 20.66 0.26 1.99 12/15/2008 1:26:29 PM - ZERO 12.46 7.49 4.22 12/15/2008 1:26:59 PM - ZERO 12.02 8.74 4.21 12/15/2008 1:27:29 PM - ZERO 11.99 8.76 4.34 12/15/2008 1:27:59 PM - ZERO 11.95 8.77 4.58 12/15/2008 1:28:29 PM - ZERO 11.9 8.79 4.74 12/15/2008 1:28:59 PM - ZERO 11.9 8.8 5.07 12/15/2008 1:29:29 PM RUN 3 - 1 11.94 8.81 4.87 12/15/2008 1:29:59 PM RUN 3 - 1 11.95 8.8 4.81 12/15/2008 1:30:29 PM RUN 3 - 1 11.96 8.8 4.73 12/15/2008 1:30:59 PM RUN 3 - 1 11.98 8.79 4.68 12/15/2008 1:31:29 PM RUN 3 - 1 11.99 8.79 4.57 12/15/2008 1:31:59 PM RUN 3 - 1 12.01 8.78 4.54 12/15/2008 1:32:29 PM RUN 3 - 1 11.98 8.79 4.74 12/15/2008 1:32:59 PM RUN 3 - 1 11.97 8.79 4.94 12/15/2008 1:33:29 PM RUN 3 - 1 11.96 8.79 5.08 12/15/2008 1:33:59 PM RUN 3 - 1 11.99 8.79 4.92 12/15/2008 1:34:29 PM RUN 3 - 1 11.98 8.78 5.25 12/15/2008 1:34:59 PM RUN 3 - 1 11.99 8.78 5.21 12/15/2008 1:35:29 PM RUN 3 - 1 11.99 8.79 5.13

Page 12 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 1:35:59 PM RUN 3 - 1 12.01 8.79 5.15 12/15/2008 1:36:29 PM RUN 3 - 1 11.99 8.79 5.21 12/15/2008 1:36:59 PM RUN 3 - 1 12 8.78 5.15 12/15/2008 1:37:29 PM RUN 3 - 1 12 8.77 5.23 12/15/2008 1:37:59 PM RUN 3 - 1 11.96 8.78 5.26 12/15/2008 1:38:29 PM RUN 3 - 1 11.96 8.76 5.33 12/15/2008 1:38:59 PM RUN 3 - 1 11.97 8.77 5.28 12/15/2008 1:39:29 PM RUN 3 - 1 11.99 8.77 5.23 12/15/2008 1:39:59 PM RUN 3 - 1 12 8.77 5.14 12/15/2008 1:40:29 PM RUN 3 - 1 12 8.77 5.17 12/15/2008 1:40:59 PM RUN 3 - 1 11.98 8.77 5.29 12/15/2008 1:41:29 PM RUN 3 - 1 11.99 8.77 5.14 12/15/2008 1:41:59 PM RUN 3 - 1 12.01 8.78 5.11 12/15/2008 1:42:29 PM RUN 3 - 1 12 8.78 5.18 12/15/2008 1:42:59 PM RUN 3 - 1 11.98 8.76 5.32 12/15/2008 1:43:29 PM RUN 3 - 1 11.97 8.78 5.3 12/15/2008 1:43:59 PM RUN 3 - 1 11.98 8.76 5.29 12/15/2008 1:44:29 PM RUN 3 - 1 11.95 8.78 5.34 12/15/2008 1:44:59 PM RUN 3 - 1 11.97 8.76 5.43 12/15/2008 1:45:29 PM RUN 3 - 1 11.96 8.78 5.32 12/15/2008 1:45:59 PM RUN 3 - 1 11.95 8.77 5.36 12/15/2008 1:46:29 PM RUN 3 - 1 11.97 8.78 5.25 12/15/2008 1:46:59 PM RUN 3 - 1 11.99 8.76 5.34 12/15/2008 1:47:29 PM RUN 3 - 1 11.94 8.8 5.53 12/15/2008 1:47:59 PM RUN 3 - 1 11.91 8.77 5.77 12/15/2008 1:48:29 PM RUN 3 - 1 11.87 8.8 5.66 12/15/2008 1:48:59 PM RUN 3 - 1 11.9 8.77 5.25 12/15/2008 1:49:29 PM RUN 3 - 1 11.91 8.77 5.15 12/15/2008 1:49:59 PM RUN 3 - 1 11.9 8.78 5.13 12/15/2008 1:50:29 PM RUN 3 - 1 11.92 8.77 5.05 12/15/2008 1:50:59 PM RUN 3 - 1 11.96 8.78 4.87 12/15/2008 1:51:29 PM RUN 3 - 1 11.95 8.76 4.87 12/15/2008 1:51:59 PM RUN 3 - 1 11.94 8.75 5.05 12/15/2008 1:52:29 PM RUN 3 - 1 11.92 8.77 5.03 12/15/2008 1:52:59 PM RUN 3 - 1 11.93 8.77 5.1 12/15/2008 1:53:29 PM RUN 3 - 1 11.93 8.77 5.11 12/15/2008 1:53:59 PM RUN 3 - 1 11.92 8.79 4.94 12/15/2008 1:54:29 PM RUN 3 - 1 11.94 8.77 4.93 12/15/2008 1:54:59 PM RUN 3 - 1 11.9 8.77 5.1 12/15/2008 1:55:29 PM RUN 3 - 1 11.94 8.77 4.94 12/15/2008 1:55:59 PM RUN 3 - 1 11.94 8.77 4.9 12/15/2008 1:56:29 PM RUN 3 - 1 11.95 8.76 4.9 12/15/2008 1:56:59 PM RUN 3 - 1 11.97 8.76 4.84 12/15/2008 1:57:29 PM RUN 3 - 1 11.97 8.76 5.24 12/15/2008 1:57:59 PM RUN 3 - 1 11.9 8.77 5.42 12/15/2008 1:58:29 PM RUN 3 - 1 11.87 8.77 5.42 12/15/2008 1:58:59 PM RUN 3 - 1 11.9 8.76 5.31 12/15/2008 1:59:29 PM RUN 3 - 1 11.95 8.75 5.15 12/15/2008 1:59:59 PM RUN 3 - 1 11.95 8.76 5.15 12/15/2008 2:00:29 PM RUN 3 - 1 11.98 8.75 5.04 12/15/2008 2:00:59 PM RUN 3 - 1 11.98 8.76 4.94 12/15/2008 2:01:29 PM RUN 3 - 1 12 8.75 4.93 12/15/2008 2:01:59 PM RUN 3 - 1 11.98 8.76 5.02 12/15/2008 2:02:29 PM RUN 3 - 1 11.98 8.75 5.15

Page 13 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 2:02:59 PM RUN 3 - 1 11.95 8.76 5.18 12/15/2008 2:03:29 PM RUN 3 - 1 11.95 8.76 5.2 12/15/2008 2:03:59 PM RUN 3 - 1 11.96 8.77 5.05 12/15/2008 2:04:29 PM RUN 3 - 1 11.95 8.76 5.18 12/15/2008 2:04:59 PM RUN 3 - 1 11.96 8.75 5.07 12/15/2008 2:05:29 PM RUN 3 - 1 11.97 8.76 4.96 12/15/2008 2:05:59 PM RUN 3 - 1 12.01 8.75 4.82 12/15/2008 2:06:29 PM RUN 3 - 1 12 8.75 4.8 12/15/2008 2:06:59 PM RUN 3 - 1 11.99 8.76 4.99 12/15/2008 2:07:29 PM RUN 3 - 1 11.96 8.75 5.07 12/15/2008 2:07:59 PM RUN 3 - 1 11.96 8.75 5.06 12/15/2008 2:08:29 PM RUN 3 - 1 11.92 8.78 4.57 12/15/2008 2:08:59 PM RUN 3 - 1 11.94 8.78 5.09 12/15/2008 2:09:29 PM RUN 3 - 1 11.96 8.76 4.95 12/15/2008 2:09:59 PM RUN 3 - 1 11.98 8.73 5.03 12/15/2008 2:10:29 PM RUN 3 - 1 11.97 8.76 5.04 12/15/2008 2:10:59 PM RUN 3 - 1 11.97 8.75 5.02 12/15/2008 2:11:29 PM RUN 3 - 1 11.98 8.74 5.06 12/15/2008 2:11:59 PM RUN 3 - 1 11.99 8.76 5.02 12/15/2008 2:12:29 PM RUN 3 - 1 12.01 8.75 4.99 12/15/2008 2:12:59 PM RUN 3 - 1 12 8.74 4.92 12/15/2008 2:13:29 PM RUN 3 - 1 11.99 8.73 4.97 12/15/2008 2:13:59 PM RUN 3 - 1 11.98 8.75 4.97 12/15/2008 2:14:29 PM RUN 3 - 1 11.98 8.75 4.93 12/15/2008 2:14:59 PM RUN 3 - 1 11.98 8.75 5.04 12/15/2008 2:15:29 PM RUN 3 - 1 11.98 8.76 5.09 12/15/2008 2:15:59 PM RUN 3 - 1 11.98 8.75 5.03 12/15/2008 2:16:29 PM RUN 3 - 1 11.98 8.75 5.16 12/15/2008 2:16:59 PM RUN 3 - 1 11.95 8.76 5.18 12/15/2008 2:17:29 PM RUN 3 - 1 11.96 8.75 5.08 12/15/2008 2:17:59 PM RUN 3 - 1 11.98 8.75 5.17 12/15/2008 2:18:29 PM RUN 3 - 1 11.96 8.77 5.15 12/15/2008 2:18:59 PM RUN 3 - 1 11.98 8.75 5.02 12/15/2008 2:19:29 PM RUN 3 - 1 11.99 8.75 4.99 12/15/2008 2:19:59 PM RUN 3 - 1 11.98 8.76 5 12/15/2008 2:20:29 PM RUN 3 - 1 11.99 8.74 4.96 12/15/2008 2:20:59 PM RUN 3 - 1 12 8.75 4.9 12/15/2008 2:21:29 PM RUN 3 - 1 12.02 8.75 4.89 12/15/2008 2:21:59 PM RUN 3 - 1 12.03 8.75 4.92 12/15/2008 2:22:29 PM RUN 3 - 1 12.03 8.75 4.87 12/15/2008 2:22:59 PM RUN 3 - 1 11.99 8.75 5.1 12/15/2008 2:23:29 PM RUN 3 - 1 11.97 8.76 5.11 12/15/2008 2:23:59 PM RUN 3 - 1 11.99 8.76 5.09 12/15/2008 2:24:29 PM RUN 3 - 1 11.98 8.76 5.06 12/15/2008 2:24:59 PM RUN 3 - 1 12 8.76 5.06 12/15/2008 2:25:29 PM RUN 3 - 1 12 8.75 4.93 12/15/2008 2:25:59 PM RUN 3 - 1 12.01 8.74 5.06 12/15/2008 2:26:29 PM RUN 3 - 1 11.99 8.76 5.06 12/15/2008 2:26:59 PM RUN 3 - 1 11.99 8.76 4.99 12/15/2008 2:27:29 PM RUN 3 - 1 12.01 8.75 4.87 12/15/2008 2:27:59 PM RUN 3 - 1 11.99 8.74 5.09 12/15/2008 2:28:29 PM RUN 3 - 1 11.96 8.74 5.26 12/15/2008 2:28:59 PM RUN 3 - 1 11.96 8.76 5.22 12/15/2008 2:29:29 PM RUN 3 - 2 11.98 8.74 5.16

Page 14 of 15LabView Log

Date Time Status aO2 (%) bCO2 (%) cCO (PPM)

12/15/2008 2:29:59 PM 11.98 8.74 5.11 12/15/2008 2:30:29 PM 12.02 8.73 10 12/15/2008 2:30:59 PM 9.09 5 3.73 12/15/2008 2:31:29 PM 10.51 8.61 0.39 12/15/2008 2:31:59 PM - Span 10.52 8.81 0.34 12/15/2008 2:32:29 PM - Span 10.52 8.83 0.33 12/15/2008 2:32:59 PM - Span 10.52 8.84 0.37 12/15/2008 2:33:29 PM - Span 10.51 8.83 0.3 12/15/2008 2:33:59 PM - Span 16.25 4.93 0.61 12/15/2008 2:34:29 PM - Span 20.79 0.23 0.63 12/15/2008 2:34:59 PM - ZERO 14.87 0.09 3.47 12/15/2008 2:35:29 PM - Span 0.2 0.06 4.72 12/15/2008 2:35:59 PM - ZERO 0.08 0.04 3.99 12/15/2008 2:36:29 PM - ZERO 0.06 0.03 3.98 12/15/2008 2:36:59 PM - ZERO 5.58 0.02 2.97 12/15/2008 2:37:29 PM - ZERO 5.14 3.01 2.75 12/15/2008 2:37:59 PM - ZERO 19.94 0.32 0.62 12/15/2008 2:38:29 PM - ZERO 20.8 0.03 0.55 12/15/2008 2:38:59 PM - ZERO 20.83 0.02 -0.01 12/15/2008 2:39:29 PM - ZERO 20.85 0.02 0.01 12/15/2008 2:39:59 PM - ZERO 18.16 2.12 2.4 12/15/2008 2:40:29 PM - ZERO 12.14 8.2 3.64 12/15/2008 2:40:59 PM - ZERO 12 8.67 3.63 12/15/2008 2:41:29 PM - ZERO 17.17 4.72 0.63 12/15/2008 2:41:59 PM - ZERO 20.84 0.24 -0.07 12/15/2008 2:42:29 PM - ZERO 20.87 0.1 -0.09

Page 15 of 15

## CYLINDER GAS CERTIFICATES

# rp KA'I'A 

# CLASS 

# iM Scott Specialty 

# Gases Dual-Analyzed 

# Calibration 

# Standard

61 41 EASTON ROAD, BLDG 1 ,PLUMSTEADVICCE,PA 1 8949-0310 Phone 

### 800-33 1-4953 Fax: 21 

### 5-766-7226



## CERTlFlCATE OF ACCURACY 

## : EPA Protocol Gas

Assay Laboratory Customer P.O. NO.: E-NO6925 TAMPA ELECTRIC COMPANY SCOTT SPECIALTY GASES Project No.: 01 -5867 1 

### -002 CHARLES DUFENY 6141 EASTON ROAD, BLDG 1 501 0 CAUSEWAY BLVD PLUMSTEADVILLE,PA 18949-03 1 0 TAMPA FL 

### 3361 9

ANALYTICAL INFORMATION This certificat~ov was performed according to €PA Traceabll~ty Protocol For Assay & Cerul~cat~on of Gaseous Calibrat~on Standards;
Procedure G-1 ; Sapteniber, 1997. Cylinder Number: ALM0220 18 Certification Date: 120ct2006 Exp. Date: 1 

### 10ct2009 Cylinder Pressure* 

### * *: 2000 PSlG ANALYTICAL COMPONENT CERTIFIED CONCENTRATION (Moles) ACCURACY* 

### * TRACEABILITY CARBON DIOXIDE 18.0 % +/- 1% Direct NtST and NMi OXYGEN 20.9 % +I- 1% 

### Direct NET and NMi NITROGEN BALANCE

*"' Do not u~e when c {l~ndur pressure 1s below 150 psig '" Analyt~cal accurdr.7 13 based on the requiremenrr ol EPA Prolocol Procedure GI. Seplemher 1997. REFERENCE STANDARD TYPEISRM NO. EXPIRATION DATE CYLINDER NUMBER



### -- CONCENTRATlON COMPONENT

NTRtd 1675 05Ju12008 KOr?1509 13.93 W CARBON DIOXIDE

MTHM 2659 04Ju12QDB KO046 10 20.85 % OXYGEN

INSTRUMENTATION INSTRUMEN-T/MODEL/SERlA~+ 

### -- DATE LAST CALIBRATED ANALYTICAL PRINCIPLE

MT I!M200/170927 ZOSep2006 GC-TCD

MTI!M?00/170927 20Sep2006 GC-TCD



### ANALYZER 

### READINGS (Z =Zero Gas R = Reference Gas T = Test Gas r =Correlation Coefficient) First Triad Analysis Second Triad Analysis Calibration Curve

Concsntratlon= A+ 0a +C#2+ 0x3 + Ex4

21 =0.00000 R1=643255 0 TI = 826324.0

R2 =643437.0 ZZ = 0,00000 T2 

# - 826277.0

23 = 0,00000 T3- 826351 0 U3 = 643355.0 8 = 2.1 778E.05
Avg. Concentration

OXY GEM

Canctwltration- At Bx +Crt t 0x3 + Ex4

2 1 = 0 00000 A1 = 536286.0 TI = 549300.0

R2 = 636629 0 22=0.00000 T2 = 549027.0 Constants: A=1.9132E-02

23 = 0 00000 T3 = 548522.0 A3 = 637922.0 B= 3.8059E-05 Aug. Concentration.



### APPROVED BY:

A

## APPENDIX B

VOLATILE ORGANIC COMPOUNDS DATA

## FIELD DATA SHEETS

## LABORATORY ANALYSIS – ENTHALPY ANALYTICAL, INC

## APPENDIX C

SULFURIC ACID MIST TEST DATA

## FIELD DATA SHEETS

## CALCULATED RUN DATA

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 1 Date: 12/15/08

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 30.08 "Hg Nozzle Area, A n : 0.00021166 ft 2 Stack Pressure, P s : 30.04 "Hg Average Orifice Meter, Δ H: 1.233 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.055 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 73.6 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 320.4 o F 12.0 % O 2 Average √ Δ p: 1.111 "H 2 O

0.0 % CO Condensate Volume, V lc : 49.9 ml 79.0 % N 2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements: V w(std) = 4.714E-02 x V lc 2.352 scf V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 36.982 dscf B ws = V w(std) / (V m(std) + V w(std) ) 0.060 % FDA = 1.0 - B ws 0.940 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.92 lb./lb. mole M s = (M d x FDA) + (18.0 x B ws ) 29.21 lb./lb. mole

v s = 85.49 x C p x ( √Δ p) x ( √ (T s + 460) / (M s x P s )) 75.23 ft/second Q s = v s x A s x 60 1279774.1 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 817322.9 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 60) 101.0 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.0101 Volume Titrant Blank, V tb 0.02 Volume Titrant Sample, V t 5.45 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 8.015E-07 lb/dscf F c -factor = 2310 dscf/mmBtu E H2SO4 = C H2SO4 x F c -factor x (100/%CO 2 ) = 0.02057 lb/mmBtu E H2SO4 = C H2SO4 x Q s(std) x 60 = 39 lb/hr

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 2 Date: 12/15/08

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 30.08 "Hg Nozzle Area, A n : 0.00021166 ft 2 Stack Pressure, P s : 30.03 "Hg Average Orifice Meter, Δ H: 1.292 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 39.137 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 79.0 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 320.9 o F 12.0 % O 2 Average √ Δ p: 1.133 "H 2 O

0.0 % CO Condensate Volume, V lc : 44.8 ml 79.0 % N 2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements: V w(std) = 4.714E-02 x V lc 2.112 scf V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 37.657 dscf B ws = V w(std) / (V m(std) + V w(std) ) 0.053 % FDA = 1.0 - B ws 0.947 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.92 lb./lb. mole M s = (M d x FDA) + (18.0 x B ws ) 29.29 lb./lb. mole

v s = 85.49 x C p x ( √Δ p) x ( √ (T s + 460) / (M s x P s )) 76.64 ft/second Q s = v s x A s x 60 1303698.2 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 837812.4 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 60) 100.3 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.0101 Volume Titrant Blank, V tb 0.02 Volume Titrant Sample, V t 8.55 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 1.237E-06 lb/dscf F c -factor = 2310 dscf/MMBtu E H2SO4 = C H2SO4 x F c -factor x (100/%CO 2 ) = 0.03174 lb/MMBtu E H2SO4 = C H2SO4 x Q s(std) x 60 = 62 lb/hr

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 3 Date: 12/15/08

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 30.02 "Hg Nozzle Area, A n : 0.00021166 ft 2 Stack Pressure, P s : 29.97 "Hg Average Orifice Meter, Δ H: 1.306 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 39.522 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 73.4 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 322.0 o F 12.0 % O 2 Average √ Δ p: 1.136 "H 2 O

0.0 % CO Condensate Volume, V lc : 48.3 ml 79.0 % N 2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements: V w(std) = 4.714E-02 x V lc 2.277 scf V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 38.356 dscf B ws = V w(std) / (V m(std) + V w(std) ) 0.056 % FDA = 1.0 - B ws 0.944 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.92 lb./lb. mole M s = (M d x FDA) + (18.0 x B ws ) 29.25 lb./lb. mole

v s = 85.49 x C p x ( √Δ p) x ( √ (T s + 460) / (M s x P s )) 77.06 ft/second Q s = v s x A s x 60 1310862.0 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 836818.8 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 60) 102.3 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.0101 Volume Titrant Blank, V tb 0.02 Volume Titrant Sample, V t 6.8 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 9.650E-07 lb/dscf F c -factor = 2310 dscf/MMBtu E H2SO4 = C H2SO4 x F c -factor x (100/%CO 2 ) = 0.02477 lb/MMBtu E H2SO4 = C H2SO4 x Q s(std) x 60 = 49 lb/hr

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 4 Date: 12/1 6 /08

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 30.00 "Hg Nozzle Area, A n : 0.00021166 ft 2 Stack Pressure, P s : 29.95 "Hg Average Orifice Meter, Δ H: 1.218 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.361 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 77.0 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 320.0 o F 12.0 % O 2 Average √ Δ p: 1.101 "H 2 O

0.0 % CO Condensate Volume, V lc : 46.1 ml 79.0 % N 2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements: V w(std) = 4.714E-02 x V lc 2.173 scf V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 36.945 dscf B ws = V w(std) / (V m(std) + V w(std) ) 0.056 % FDA = 1.0 - B ws 0.944 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.92 lb./lb. mole M s = (M d x FDA) + (18.0 x B ws ) 29.26 lb./lb. mole

v s = 85.49 x C p x ( √Δ p) x ( √ (T s + 460) / (M s x P s )) 74.60 ft/second Q s = v s x A s x 60 1269064.4 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 812109.4 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s x 60) 101.6 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.0101 Volume Titrant Blank, V tb 0.02 Volume Titrant Sample, V t 3.82 Volume of Sample Aliquot, V a 50 Total Volume of Solution, V soln 250

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 5.615E-07 lb/dscf F c -factor = 2310 dscf/MMBtu E H2SO4 = C H2SO4 x F c -factor x (100/%CO 2 ) = 0.01441 lb/MMBtu E H2SO4 = C H2SO4 x Q s(std) x 60 = 27 lb/hr

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 5 Date: 12/1 6 /08

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 30.00 "Hg Nozzle Area, A n : 0.00021166 ft 2 Stack Pressure, P s : 29.95 "Hg Average Orifice Meter, Δ H: 1.230 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 38.735 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 87.8 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 322.2 o F 12.0 % O 2 Average √ Δ p: 1.097 "H 2 O

0.0 % CO Condensate Volume, V lc : 42.7 ml 79.0 % N 2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements: V w(std) = 4.714E-02 x V lc 2.013 scf V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 36.569 dscf B ws = V w(std) / (V m(std) + V w(std) ) 0.052 % FDA = 1.0 - B ws 0.948 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.92 lb./lb. mole M s = (M d x FDA) + (18.0 x B ws ) 29.30 lb./lb. mole

v s = 85.49 x C p x ( √Δ p) x ( √ (T s + 460) / (M s x P s )) 74.40 ft/second Q s = v s x A s x 60 1265685.7 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 810552.2 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s 100.7 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.0101 Volume Titrant Blank, V tb 0.02 Volume Titrant Sample, V t 5.25 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 7.807E-07 lb/dscf F c -factor = 2310 dscf/MMBtu E H2SO4 = C H2SO4 x F c -factor x (100/%CO 2 ) = 0.02004 lb/MMBtu E H2SO4 = C H2SO4 x Q s(std) x 60 = 38 lb/hr

### Environmental Services A ir Services Group

40 CFR 60, Appendix A - Test Methods Reference Method 8

Test Calculations

Customer: Polk Power Station Facility: Unit 1 Sampling Location: Stack Operating Conditions: Full Load Run Number: 6 Date: 12/1 6 /08

Sample Time, θ : 60 minutes Nozzle Diameter, D n : 0.197 inches Barometric Pressure, P b : 30.00 "Hg Nozzle Area, A n : 0.00021166 ft 2 Stack Pressure, P s : 29.95 "Hg Average Orifice Meter, Δ H: 1.259 "H 2 O Effective Stack Area, A s : 283.529 ft 2 Sample Volume, V m : 39.723 ft 3 Pitot Coefficient, Cp: 0.84 dimensionless Average Meter Temp., T m : 98.5 o F Gas Analysis: 9.0 % CO 2 Average Stack Temp., T s : 322.0 o F 12.0 % O 2 Average √ Δ p: 1.099 "H 2 O

0.0 % CO Condensate Volume, V lc : 47.8 ml 79.0 % N 2 Meter Box Y: 0.974 dimensionless

Data Calculated from Source Measurements: V w(std) = 4.714E-02 x V lc 2.253 scf V m(std) = 17.647 x V m x Y x (P b + ( Δ H / 13.6)) / (T m +460) 36.791 dscf B ws = V w(std) / (V m(std) + V w(std) ) 0.058 % FDA = 1.0 - B ws 0.942 % M d = (0.44 x %CO 2 ) + (0.32 x %O 2 ) + (0.28 x (%N 2 + % CO)) 29.92 lb./lb. mole M s = (M d x FDA) + (18.0 x B ws ) 29.23 lb./lb. mole

v s = 85.49 x C p x ( √Δ p) x ( √ (T s + 460) / (M s x P s )) 74.60 ft/second Q s = v s x A s x 60 1269097.6 acf/minute Q s(std) = Q s x FDA x (528 / (T s + 460)) x (P s / 29.92)) 808202.2 dscf/minute I = (T s + 460) x ((2.67E-03 x V lc ) + (V m(std) / 17.647)) x 100 / ( θ x P s x A n x v s 101.6 %

Data from Laboratory Analysis: H 2 SO 4 Normality of Barium Chloride titrant, N 0.0101 Volume Titrant Blank, V tb 0.02 Volume Titrant Sample, V t 5.48 Volume of Sample Aliquot, V a 100 Total Volume of Solution, V soln 500

Calculated Concentration and Emission Rate Data:

C H2SO4 = 1.081E-04 x (N x (V t - V tb ) x (V soln / V a )) / V m(std) = 8.102E-07 lb/dscf F c -factor = 2310 dscf/MMBtu E H2SO4 = C H2SO4 x F c -factor x (100/%CO 2 ) = 0.02079 lb/MMBtu E H2SO4 = C H2SO4 x Q s(std) x 60 = 39 lb/hr

## LABORATORY ANALYSIS

## Laboratory Services 5012 Causeway Blvd * Tampa Fl. 33619 * Ph (813)630-7378 * Fax (813)630-7360 * DOH #E54272 

### Report For: 

## Laboratory ID: AA98712

Date and Time Collected: Sampled By: 

## Sample Information

SCOTT GIVEN Description: 

## Location Code: 01/26/2009 Report Date:

Polk No. 1 Acid Mist Comp on Syngas 

## TE_PPS_1_SAM_SYNGAS

Project Account Code: 12/17/2008 Date of Sample Receipt: Sample Collection Method: 

## Laboratory Results 12/15/2008 12:00:00 AM

Result PARAMETER Qualifier Code Test Method Analyst Units Upper Limit MDL Violation Check Analysis Date & Time Lower Limit Normality of BaCl2 * 2H2O 0.0001 KARXL 0.0101 12/17/2008 1:00:00 PM
SO3, Avg. of Blank Titrations milliliters 0.01 EPA - Meth.8 KARXL 0.02 I 12/17/2008 1:00:00 PM
SO3, Run #1, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 5.45 12/17/2008 1:00:00 PM
SO3, Run #2, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 8.55 12/17/2008 1:00:00 PM
SO3, Run #3, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 6.80 12/17/2008 1:00:00 PM
SO3, Run #4, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 3.82 12/17/2008 1:00:00 PM
SO3, Run #5, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 5.25 12/17/2008 1:00:00 PM
SO3, Run #6, Avg. of Titrations milliliters 0.01 EPA - Meth.8 KARXL 5.48 12/17/2008 1:00:00 PM
SO3, Volume of Contained Sample milliliters 1 EPA - Meth.8 KARXL see comment 12/17/2008 1:00:00 PM
SO3, Volume of Sample Aliquot milliliters 0.1 EPA - Meth.8 KARXL see comment 12/17/2008 1:00:00 PM 

## Comments

Ray McDarby,

Manager, Laboratory Services I - The reported value is between the laboratory method detection limit (MDL) and the laboratory pr actical quantitation limit ( PQL). PQL = 4 x MDL. All results calculated on a wet to wet basis, unless otherwise indicated. Data Qualifier Codes Explanation:

Should there be any questions regar ding this report, please contact:

(813) 630-7878 For Peggy Penner,

Report Number: 

### Page 1 of 1 "General Report" AA98712-012609-19 All of the results presented in this r eport pertain to results for sample AA98712

## EQUIPMENT CALIBRATIONS

## Environmental Service s A ir Services Grou p



## SUMMARY OF E Q UIPMENT CALIBRATION S

EQUIPMENT CAL DATE METHOD RESULTS

CONSOLE (MB 07) USEPA RM 5 INITIA L 10/24/2008 (ORIFICE) 0.974 POST TEST 12/17/2008 0.986

NOZZLE (SN16) CALIPER INITIA L 10/24/2008 MEASUREMENTS 0.197 POST TEST 12/17/2008 0.198

PYROMETER (PY 09) 10/24/2008 ASTM THERMOMETER + 2 o 

## F

PITOT TUBE (PT 11) 10/24/2008 USEPA RM 2 C p 

## = 0.84

BAROMETER (BR 06) 12/05/2008 NWS COMPARISON + 0.01" Hg

## Environmental Services Air Services Group

Blue Team Manufacturer: Thermo Anderson Calibration Date: Model Number:MST-C1 Barometric Pressure: 29.93 "Hg Instrument Code Number: ^MB07 Theoretical Critical Vacuum: 14.12 "Hg LabWorks Sample Number: Calibrated By:

Initial Final Total Δ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes ft 3 

### ft 3 

### ft 3 

### oF oF oF oF 0.63 15 130.700 137.750 7.050 79 74 80 75 1.15 15 154.500 163.894 9.394 86 77 85 78 1.90 15 141.910 153.917 12.007 83 75 86 77 3.55 15 164.650 181.150 16.500 86 79 94 81

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 48 0.3448 23.0 72 72 72.0 55 0.4593 21.5 72 72 72.0 63 0.5917 19.5 72 72 72.0 73 0.8101 16.5 72 72 72.0

Dry Gas Meter Calibration Calibration Volume Volume Volume Y Δ H α Corrected Corrected Nominal Value QA/QC Value QA/QC Vm (std) 

### , ft 3 

### Vcr (std) 

### , ft 3 

### Vcr (std) 

### , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2

6.942 6.711 6.763 0.967 -0.007 1.741 -0.019 9.185 8.940 9.008 0.973 0.000 1.776 0.016 11.789 11.517 11.605 0.977 0.003 1.772 0.012 16.124 15.768 15.889 0.978 0.004 1.751 -0.009 Averages: 0.974 1.760

Review/Approval:

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02. For Calibration Δ H α , the acceptable tolerance of individual values from the average is + 0.2.



### 29-Oct-08 Critical Orifice Readings Ambient Temperatures

CALCULATED DATA Critical Orifice The Critical Orifice Coefficient, K', should be in English units. 

### IMPORTANT Dry Gas Meter Readings Initial Temperatures Final Tempertures 10/24/2008

GDB

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. 

## USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method Quarterly Calibration

## Environmental Services Air Services Group

Manufacturer: THERMO Calibration Date: Model Number:MST Barometric Pressure: 30.26 "Hg Instrument Code Number: MB07 Theoretical Critical Vacuum: 14.27 "Hg LabWorks Sample Number: Calibrated By: A ssociated Test: Team: BLUE

Initial Final Total Δ H Time Volume Volume Volume Inlet Outlet Inlet Outlet "H 2 

### O Minutes ft 3 

### ft 3 

### ft 3 

### oF oF oF oF

1.1 10 847.200 853.335 6.135 76 72 76 71 1.1 10 853.335 859.460 6.125 76 71 77 71 1.1 10 859.460 865.575 6.115 77 72 77 72

Orifice K' A ctual Serial Orifice Vacuum Initial Final Average Number Coefficient "Hg oF oF oF 55 0.4596 20.5 68 68 68.0 55 0.4596 20.5 68 68 68.0 55 0.4596 20.5 68 68 68.0

Dry Gas Meter Calibration Calibration Volume Volume Volume Y Δ H α Corrected Corrected Nominal Value QA/QC Value QA/QC Vm (std) 

### , ft 3 

### Vcr (std) 

### , ft 3 

### Vcr (std) 

### , ft 3 

### (ratio) + 0.02 "H 2 

### O + 0.2

6.152 6.052 5.987 0.984 -0.002 1.690 0.001 6.142 6.052 5.987 0.985 0.000 1.690 0.001 6.123 6.052 5.987 0.988 0.003 1.687 -0.002 Averages: 0.986 1.689 Prior Y: 0.974 % Difference:(+/-5%) -1.22% PASS

Review/Approval: Date: 5-Jan-09 CALCULATED DATA

For Calibration Y, the ratio of the reading of the calibration orifice to the dry gas meter, acceptable tolerance from average is + 0.02. For Calibration Δ H α , the acceptable tolerance of individual values from the average is + 0.2. 

### Critical Orifice 

## USEPA Reference Method 5

Dry Gas Meter Calibration

Critical Orifice Method

SEG 12/17/2008 

## POST - TEST CALIBRATION CHECK

Ambient Temperatures Dry Gas Meter Readings Final Tempertures Initial Temperatures

Critical Orifice Readings POLK SAP-UNIT 1 IMPORTANT

IMPORTANT For valid test results, the Actual Vacuum should be 1 to 2 "Hg greater than the Theoretical Critical Vacuum Shown above. The Critical Orifice Coefficient, K', should be in English units.

## Calibration Date: Responsible Party:

Nozzle Maximum 

## Average

I.D. D 1 

## D 2 

## D 3 

### D ifference, " 

## D n 

## , inches ^SN01 0.110 0.110 0.119 0.004 0.113 ^SN04 0.121 0.121 0.120 0.000 0.121 ^SN05 0.147 0.147 0.145 0.001 0.146 ^SN06 0.197 0.196 0.195 0.001 0.196 ^SN09 0.270 0.270 0.271 0.000 0.270 ^SN10 0.294 0.295 0.296 0.001 0.295 ^SN12 0.387 0.386 0.388 0.001 0.387 ^SN15 0.163 0.164 0.163 0.000 0.163 ^SN16 0.198 0.197 0.197 0.000 0.197 ^SN19 0.278 0.280 0.279 0.001 0.279 ^SN22 0.366 0.366 0.367 0.000 0.366 ^SN30 0.311 0.310 0.312 0.001 0.311 ^SN36 0.184 0.184 0.182 0.001 0.183 ^SN37 0.210 0.209 0.209 0.000 0.209 ^SN38 0.252 0.250 0.252 0.001 0.251 ^SN46 0.189 0.188 0.187 0.001 0.188 ^SN47 0.203 0.204 0.203 0.000 0.203 ^SN48 0.252 0.252 0.251 0.000 0.252 ^SN50 0.309 0.311 0.312 0.001 0.311 ^SN58 0.243 0.246 0.246 0.001 0.245 ^SN68 0.252 0.250 0.250 0.001 0.251 ^SN69 0.371 0.370 0.374 0.002 0.372 ^SN70 0.616 0.614 0.614 0.001 0.615 ^SN71 0.614 0.614 0.612 0.001 0.613 ^SN72 0.372 0.372 0.373 0.000 0.372 ^SN73 0.510 0.510 0.509 0.000 0.510 ^SN74 0.483 0.482 0.482 0.000 0.482



## QA/QC Review by: 29-Oct-08 Nozzle Diameter, D n 

## (in) QUARTERLY NOZZLE CALIBRATIONS

STEEL NOZZLE SET

10/24/2008 RN/JV

## Environmental Service s A ir Services Grou p

Shared Resource Calibration Date: Calibration Personnel: Test Designation:

Maximum 

## Average D 1 

## D 2 

## D 3 

### Difference, " 

## D n 

## , inches 0.197 0.198 0.198 0.001 0.198

Data Notations: Maximum Difference must be < 0.004".



## Quarterly (pre-test) value for nozzle ID SN16 was 0.197

Difference (Pre-test/Post-test) is: -0.001 PASS

QA/QC Review by: 5-Jan-09 SN16 POST TEST NOZZLE CALIBRATION

Nozzle Identifier Nozzle Diameter, D n 

## (in) 12/17/2008 SEG POLK 1-SAM

## Environmental Services A ir Services Group

Blue Team Pyrometer Under Tes t Pyrometer Number: ^PY09 Labworks Sample # Calibration Date: 10/24/2008

Calibrator Information Calibrator Type/Manufacturer: Hart Scientific Calibrator Serial Number: A OA024 Date of Last Calibration: 04/28/2008 Calibration Personnel (Typed and Signature):

Calibration Data

Calibration Reference Pyrometer Point Temperature Indication Difference

1 

## 400 402 -2 2 

## 212 214 -2 3 

## 32 33 -1

Reference temperatures must encompass the expected range of measurement. These three points should be ~ 32 degrees, ~212 degrees, and ~ 400 degrees Farenheit. Difference is calculated as follows:

(reference temperature ) – (pyrometer indication )

Qaulity Control Data

Calibration Point Difference

1 

## Pass 2 

## Pass 3 

## Pass

Reviewer: 

## 0

Varino 

## Pyrometer Calibration

29-Oct-08

### Pitot Tube ID # Calibration Date Operating Quarter/Year: 4-08 Openings Damaged? ___ Y

_ _

_ N Repaired?

_ __ _ Y ___ N ___ N/A

Labworks #:

Alpha and Beta Angle Determinations Acceptable Limits:



### α 1 

### 1.4 degrees Dt 0.48 < Dt > 0.95 cm



### α 2 

### 1.5 degrees α < 10 degrees 

### β 1 

### 0.7 degrees β 2 

### 0.4 degrees β 1 < 5 degrees (alongside top impact openings) 

### Gamma, Theta, Α

, Ζ

, and W Determination s β 2 < 5 degrees (alongside bottom impact openings)



### ψ 0.2 degrees Ζ < 0.32 cm ( Α sin ψ ) 

### Α 2.37 cm W < 0.08 cm (Asin ο )


### Ζ 0.008 cm Α distance between tips

ο angle of plane on side of pitots



### ο 1.7 degrees ψ angle between tips 

### W 0.070 cm



### Comments:

Calibrated by:

Q uality Assurance Review / Approval: 29-Oct-08 details are found in EPA/600/4-77/027b, "Quality Assurance Handbook for Air Pollution Measurement Systems: Stationary Source Specific Methods", sub-section 3.1.1, Procuement of Apparatus and Supplies.



### REMOVABLE Pass

NOTES All measurements are taken in accordance with the requirements of 40 CFR 60, Appendix A - Test Methods, Method 2, "Determination of stack gas velocity and volumetric flow rate (Type S pitot tube)". Measurement 

### Pass Pass ( α 1 measured across top impact openings) 

### Pass ( α 2 measured across bottom impact openings) 

### Shared Resource

0

Pass Pass

PITOT TUBE CALIBRATION DATA SHEET

PT11

10/24/2008

## Environmental Services Air Services Group

Blue Team Instrument Number: Calibration Date: Calibration Personnel: Labworks #: Difference T ime "H g 11:00 -0.01 12:00 0 13:00 0

Avera g e Difference: -0.00333

Note: Barometric readin g s must a g ree within ± 0.1 "H g

. Current Reference is National Weather Service, TIA.

Comments (Note any ad j ustments):

QA/QC Review by: Date: 5-Dec-08 Current Conditions at Tampa International Airport 30.19 30.19 30.21 30.22 30.20 30.20 Barometer Readin g Reference Readin g

Inches Mercury Inches Mercury BAROMETER CALIBRATION

^BR06 12/05/2008 SEG

## APPENDIX D

TURBINE DATA

## PI Ops Data Run 1

Plant Information Source: polk-1pisrv Start Time: 12/15/2008 9:46

End Time: 12/15/2008 11:04 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 173.0594743 6760.14281 71.7420986 2.82809007 15-Dec-08 09:46:00 173.0626984 6759.94385 68.597702 2.82734466 15-Dec-08 09:47:00 173.2358551 6767.25293 68.6590958 2.82736373 15-Dec-08 09:48:00 173.4090118 6777.07959 68.4141541 2.8273828 15-Dec-08 09:49:00 173.5586243 6757.37695 68.4911499 2.82740211 15-Dec-08 09:50:00 172.7401886 6728.31152 68.5681458 2.82742119 15-Dec-08 09:51:00 172.0959778 6734.30322 68.6451416 2.82744026 15-Dec-08 09:52:00 172.40242 6734.11816 68.8714294 2.82745934 15-Dec-08 09:53:00 172.5999756 6737.15869 69.0018921 2.82747841 15-Dec-08 09:54:00 173.3674164 6750.79541 69.0018921 2.82749748 15-Dec-08 09:55:00 173.2668457 6755.28076 69.0018921 2.82751679 15-Dec-08 09:56:00 173.4589691 6735.10107 69.0018921 2.82753587 15-Dec-08 09:57:00 173.2593384 6745.36816 69.3312225 2.82755494 15-Dec-08 09:58:00 173.75914 6759.8457 69.3824158 2.82757401 15-Dec-08 09:59:00 173.6784058 6774.84912 69.433609 2.82759309 15-Dec-08 10:00:00 172.9620209 6750.18066 69.4847946 2.82761216 15-Dec-08 10:01:00 173.9638824 6774.19824 69.5359879 2.82763147 15-Dec-08 10:02:00 173.6444397 6778.63232 69.5871811 2.82765055 15-Dec-08 10:03:00 172.0343018 6729.12646 69.3434753 2.82766962 15-Dec-08 10:04:00 172.4185333 6740.58887 69.4987411 2.82768869 15-Dec-08 10:05:00 172.8027649 6746.29688 69.3264389 2.82770777 15-Dec-08 10:06:00 172.9741821 6747.9585 69.4026184 2.82772684 15-Dec-08 10:07:00 172.5327759 6791.24561 69.4787979 2.82774615 15-Dec-08 10:08:00 172.9446106 6791.55762 69.5549774 2.82776523 15-Dec-08 10:09:00 172.8365326 6747.40186 69.6311569 2.8277843 15-Dec-08 10:10:00 172.7392731 6763.67139 69.7073364 2.82780337 15-Dec-08 10:11:00 172.7933197 6774.20898 69.7835159 2.82782245 15-Dec-08 10:12:00 172.1694031 6762.30859 69.8596954 2.82784152 15-Dec-08 10:13:00 171.9230499 6740.47266 69.9358749 2.82786083 15-Dec-08 10:14:00 172.055954 6735.87695 70.0120544 2.82787991 15-Dec-08 10:15:00 172.859436 6753.11133 70.0882339 2.82789898 15-Dec-08 10:16:00 173.3289948 6770.34521 70.1644135 2.82791805 15-Dec-08 10:17:00 174.1051636 6780.58789 70.240593 2.82793713 15-Dec-08 10:18:00 173.4714203 6767.16846 70.4164658 2.8279562 15-Dec-08 10:19:00 173.3071747 6759.58887 70.2612 2.82797551



## Page 1 of 3

## PI Ops Data Run 1

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 15-Dec-08 10:20:00 172.1000519 6747.9707 70.6729202 2.82799459 15-Dec-08 10:21:00 171.7844238 6733.9585 70.8046036 2.82801366 15-Dec-08 10:22:00 172.6538696 6755.76367 70.9362946 2.82803273 15-Dec-08 10:23:00 173.2496796 6768.34668 71.0679779 2.82805181 15-Dec-08 10:24:00 173.7445374 6785.41553 71.1996613 2.82807088 15-Dec-08 10:25:00 174.1471405 6774.04883 71.3313522 2.82809019 15-Dec-08 10:26:00 172.9082794 6769.0376 71.4630356 2.82810926 15-Dec-08 10:27:00 172.9929352 6772.7041 71.4981537 2.82812834 15-Dec-08 10:28:00 173.1842957 6732.05762 71.8919983 2.82814741 15-Dec-08 10:29:00 172.2243195 6723.48584 72.0046463 2.82816648 15-Dec-08 10:30:00 173.2681732 6744.98877 72.1172867 2.82818556 15-Dec-08 10:31:00 173.9848938 6783.70459 72.2299271 2.82820463 15-Dec-08 10:32:00 173.9623718 6765.53564 72.3425751 2.82822394 15-Dec-08 10:33:00 173.5643311 6769.12891 72.4552155 2.82824302 15-Dec-08 10:34:00 173.3208771 6752.3291 72.5186386 2.82826209 15-Dec-08 10:35:00 172.3071442 6749.02881 72.8810959 2.82828116 15-Dec-08 10:36:00 172.4146423 6745.72852 73.003891 2.82830024 15-Dec-08 10:37:00 172.8871918 6747.66797 73.1266861 2.82831931 15-Dec-08 10:38:00 172.967804 6762.56543 73.2494736 2.82833862 15-Dec-08 10:39:00 173.0484161 6752.75049 73.3722687 2.8283577 15-Dec-08 10:40:00 172.9184875 6730.57422 73.6122818 2.82837677 15-Dec-08 10:41:00 173.0204163 6728.92236 73.5044861 2.82839584 15-Dec-08 10:42:00 173.2832336 6743.4248 73.6584854 2.82841492 15-Dec-08 10:43:00 173.407486 6744.34717 73.8124771 2.82843399 15-Dec-08 10:44:00 174.0248108 6778.74268 73.9664688 2.8284533 15-Dec-08 10:45:00 173.8222351 6757.25732 74.007988 2.82847238 15-Dec-08 10:46:00 173.1537781 6779.42334 73.8552475 2.82849145 15-Dec-08 10:47:00 173.0285034 6753.93896 73.850029 2.82851052 15-Dec-08 10:48:00 172.2003021 6742.71582 73.889473 2.8285296 15-Dec-08 10:49:00 172.7046051 6767.55859 74.3514557 2.82854867 15-Dec-08 10:50:00 172.7745972 6749.83301 74.4156189 2.82856798 15-Dec-08 10:51:00 173.5269623 6780.70801 74.5696106 2.82858706 15-Dec-08 10:52:00 173.9883423 6796.93555 74.7236023 2.82860613 15-Dec-08 10:53:00 173.2201691 6772.05371 74.877594 2.8286252 15-Dec-08 10:54:00 172.5875397 6770.23535 74.742424 2.82864428 15-Dec-08 10:55:00 172.7230682 6770.71777 74.7514114 2.82866335 15-Dec-08 10:56:00 172.6773834 6785.85254 75.1592026 2.82868266 15-Dec-08 10:57:00 173.3948822 6814.75586 75.5670013 2.82870173 15-Dec-08 10:58:00 173.7415924 6797.3999 75.9041977 2.82872081 15-Dec-08 10:59:00 172.0879211 6748.1499 75.6287231 2.82873988



## Page 2 of 3

## PI Ops Data Run 1

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 15-Dec-08 11:00:00 172.8661499 6769.60498 75.7852859 2.82875896 15-Dec-08 11:01:00 173.9151001 6787.28564 75.6242981 2.82877803 15-Dec-08 11:02:00 174.4136963 6791.31885 75.7264023 2.82879734 15-Dec-08 11:03:00 172.9187927 6784.37939 75.8285141 2.82881641 15-Dec-08 11:04:00 172.8209381 6747.6167 75.9306183 2.82883549



## Page 3 of 3

## PI Ops Data Run 2

Plant Information Source: polk-1pisrv Start Time: 12/15/2008 11:44

End Time: 12/15/2008 12:57 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 173.005128 6768.49807 76.6046432 2.83029763 15-Dec-08 11:44:00 172.4010468 6732.06982 76.851532 2.8296001 15-Dec-08 11:45:00 173.7168121 6833.3252 76.720459 2.82961917 15-Dec-08 11:46:00 173.9635773 6757.3418 76.589386 2.82963824 15-Dec-08 11:47:00 172.8969421 6758.20215 76.458313 2.82965732 15-Dec-08 11:48:00 172.1069336 6759.0625 76.32724 2.82967639 15-Dec-08 11:49:00 172.2890472 6741.14063 76.196167 2.82969546 15-Dec-08 11:50:00 172.4711609 6716.95801 76.065094 2.82971478 15-Dec-08 11:51:00 172.6532745 6720.13525 75.934021 2.82973385 15-Dec-08 11:52:00 172.3290863 6733.26172 75.934021 2.82975292 15-Dec-08 11:53:00 172.7487335 6752.76855 76.247139 2.829772 15-Dec-08 11:54:00 173.1809998 6798.604 75.6516953 2.82979107 15-Dec-08 11:55:00 174.0948334 6777.42822 75.7902908 2.82981014 15-Dec-08 11:56:00 173.6275787 6757.62744 75.6362915 2.82982945 15-Dec-08 11:57:00 173.4067383 6789.52881 75.7325058 2.82984853 15-Dec-08 11:58:00 172.3660889 6787.30566 75.856514 2.8298676 15-Dec-08 11:59:00 173.3027191 6768.94141 75.9805222 2.82988667 15-Dec-08 12:00:00 173.2371979 6768.91162 76.1045303 2.82990575 15-Dec-08 12:01:00 173.0919189 6775.54883 76.2285385 2.82992482 15-Dec-08 12:02:00 173.8414612 6782.18604 76.1593933 2.82994413 15-Dec-08 12:03:00 173.6455231 6762.66943 76.0561676 2.82996321 15-Dec-08 12:04:00 173.100708 6764.68604 75.9529419 2.82998228 15-Dec-08 12:05:00 172.17659 6733.88477 76.0849304 2.83000135 15-Dec-08 12:06:00 172.9056396 6764.41113 76.269722 2.83002043 15-Dec-08 12:07:00 173.3415985 6787.14502 76.4545135 2.8300395 15-Dec-08 12:08:00 173.1659851 6779.71484 76.6393051 2.83005881 15-Dec-08 12:09:00 173.2914734 6765.896 76.8240967 2.83007789 15-Dec-08 12:10:00 173.0330048 6762.21094 76.76091 2.83009696 15-Dec-08 12:11:00 173.1410675 6762.21094 76.6075439 2.83011603 15-Dec-08 12:12:00 173.5596771 6762.21094 76.4541779 2.83013511 15-Dec-08 12:13:00 173.4306183 6773.76123 76.3008194 2.83015418 15-Dec-08 12:14:00 172.6535034 6742.95996 76.3798752 2.83017349 15-Dec-08 12:15:00 172.3942261 6760.01074 76.5840836 2.83019257 15-Dec-08 12:16:00 172.6193542 6749.79785 76.7882919 2.83021164 15-Dec-08 12:17:00 173.1296539 6817.91943 76.8733749 2.83023071



## Page 1 of 2

## PI Ops Data Run 2

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 15-Dec-08 12:18:00 173.1124268 6745.68555 76.8733749 2.83024979 15-Dec-08 12:19:00 172.324585 6762.8833 77.0171051 2.83026886 15-Dec-08 12:20:00 172.6633148 6769.1167 77.0403748 2.83028817 15-Dec-08 12:21:00 173.175293 6768.18018 76.8733749 2.83030725 15-Dec-08 12:22:00 172.8448639 6743.40039 76.8733749 2.83032632 15-Dec-08 12:23:00 173.3446655 6778.56982 77.137146 2.83034539 15-Dec-08 12:24:00 173.7305756 6767.84668 77.0350418 2.83036447 15-Dec-08 12:25:00 172.9767303 6760.98828 76.9329376 2.83038354 15-Dec-08 12:26:00 173.390976 6775.646 77.1454315 2.83040285 15-Dec-08 12:27:00 173.6652527 6795.81689 77.0427704 2.83042192 15-Dec-08 12:28:00 173.4738007 6781.96826 76.9401093 2.830441 15-Dec-08 12:29:00 172.9471588 6752.55518 76.9378433 2.83046007 15-Dec-08 12:30:00 172.3932648 6749.25488 77.1220322 2.83047915 15-Dec-08 12:31:00 173.2393951 6790.48145 77.306221 2.83049822 15-Dec-08 12:32:00 172.8953094 6748.75391 77.4904099 2.83051753 15-Dec-08 12:33:00 173.6369781 6787.76855 77.6745987 2.8305366 15-Dec-08 12:34:00 174.0136108 6789.46338 77.7742386 2.83055568 15-Dec-08 12:35:00 173.1564941 6766.98145 77.6202469 2.83057475 15-Dec-08 12:36:00 172.8784637 6762.60596 77.2481003 2.83059382 15-Dec-08 12:37:00 172.6004333 6758.22998 77.3866882 2.8306129 15-Dec-08 12:38:00 172.322403 6755.90918 76.7707138 2.83063221 15-Dec-08 12:39:00 172.0586853 6762.43506 76.5188522 2.83065128 15-Dec-08 12:40:00 172.6395416 6754.979 76.2083206 2.83067036 15-Dec-08 12:41:00 173.2203979 6747.52344 76.2558975 2.83068943 15-Dec-08 12:42:00 172.4950867 6745.09717 76.343483 2.8307085 15-Dec-08 12:43:00 173.3929291 6774.31152 76.4310684 2.83072758 15-Dec-08 12:44:00 173.1497803 6823.44678 76.5186539 2.83074689 15-Dec-08 12:45:00 172.5468597 6794.44824 76.6062393 2.83076596 15-Dec-08 12:46:00 172.8034363 6796.46484 76.6938248 2.83078504 15-Dec-08 12:47:00 172.6923065 6803.375 76.7814102 2.83080411 15-Dec-08 12:48:00 172.2337799 6822.40137 76.8689957 2.83082318 15-Dec-08 12:49:00 172.4930573 6780.27051 76.8150482 2.83084226 15-Dec-08 12:50:00 173.544281 6788.22021 76.7536545 2.83086157 15-Dec-08 12:51:00 173.772049 6793.62305 76.6922607 2.83088064 15-Dec-08 12:52:00 173.3268127 6786.28955 76.6308594 2.83089972 15-Dec-08 12:53:00 173.2579956 6778.95605 76.5694656 2.83091879 15-Dec-08 12:54:00 172.8797607 6763.5874 76.8220444 2.83093786 15-Dec-08 12:55:00 172.5119019 6718.19092 76.7032013 2.83095694 15-Dec-08 12:56:00 172.3059692 6736.69873 76.4989929 2.83097625 15-Dec-08 12:57:00 172.954071 6786.59521 76.2947845 2.83099532



## Page 2 of 2

## PI Ops Data Run 3

Plant Information Source: polk-1pisrv Start Time: 12/15/2008 13:23

End Time: 12/15/2008 14:31 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 173.169507 6760.15128 76.1822533 2.83214201 15-Dec-08 13:23:00 171.5643768 6713.1123 73.8207855 2.83149219 15-Dec-08 13:24:00 173.2479401 6757.62305 73.7200775 2.83151126 15-Dec-08 13:25:00 173.6364899 6775.92627 73.5660858 2.83153033 15-Dec-08 13:26:00 173.9234924 6784.15039 73.4462891 2.83154941 15-Dec-08 13:27:00 172.8862915 6753.21826 73.4974823 2.83156872 15-Dec-08 13:28:00 173.1447144 6773.05566 73.5486755 2.83158779 15-Dec-08 13:29:00 173.6054535 6762.23828 73.5998611 2.83160686 15-Dec-08 13:30:00 171.4996796 6745.94873 73.6510544 2.83162594 15-Dec-08 13:31:00 172.6348114 6709.32178 73.7022476 2.83164501 15-Dec-08 13:32:00 173.4101868 6737.33789 73.7354813 2.83166409 15-Dec-08 13:33:00 174.4727936 6778.8335 73.4690704 2.8316834 15-Dec-08 13:34:00 173.2949066 6773.73438 74.0639954 2.83170247 15-Dec-08 13:35:00 173.6048584 6731.08008 74.2179871 2.83172154 15-Dec-08 13:36:00 173.0282135 6761.3125 74.3719864 2.83174062 15-Dec-08 13:37:00 172.9110107 6770.79102 74.5259781 2.83175969 15-Dec-08 13:38:00 173.3613892 6791.89355 74.6799698 2.83177876 15-Dec-08 13:39:00 173.8928528 6779.53809 74.4717407 2.83179808 15-Dec-08 13:40:00 173.807785 6792.21826 74.5749664 2.83181715 15-Dec-08 13:41:00 173.5557098 6791.85352 74.6781921 2.83183622 15-Dec-08 13:42:00 173.682251 6791.48877 74.377121 2.8318553 15-Dec-08 13:43:00 173.3037872 6785.84375 74.7621002 2.83187437 15-Dec-08 13:44:00 172.3973846 6750.27588 75.2240829 2.83189344 15-Dec-08 13:45:00 172.1986542 6719.93115 75.4784546 2.83191276 15-Dec-08 13:46:00 172.570282 6723.5874 75.6809311 2.83193183 15-Dec-08 13:47:00 172.5708771 6744.85498 75.8834 2.8319509 15-Dec-08 13:48:00 172.1663818 6748.87207 75.6208954 2.83196998 15-Dec-08 13:49:00 173.0457458 6767.14307 76.0592651 2.83198905 15-Dec-08 13:50:00 172.6385193 6738.35205 76.0045624 2.83200812 15-Dec-08 13:51:00 172.7263031 6747.96582 76.1077881 2.83202744 15-Dec-08 13:52:00 173.2438507 6756.34424 76.2110138 2.83204651 15-Dec-08 13:53:00 173.0811462 6753.04395 76.6249237 2.83206558 15-Dec-08 13:54:00 172.8506012 6728.63867 76.7270279 2.83208466 15-Dec-08 13:55:00 173.0730591 6746.07715 76.8291321 2.83210373 15-Dec-08 13:56:00 174.0304565 6805.3877 76.916832 2.8321228



## Page 1 of 2

## PI Ops Data Run 3

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 15-Dec-08 13:57:00 174.2365875 6787.3374 76.993515 2.83214211 15-Dec-08 13:58:00 173.8283386 6781.28711 77.0701981 2.83216119 15-Dec-08 13:59:00 173.4200897 6776.69434 77.1468811 2.83218026 15-Dec-08 14:00:00 173.3310852 6776.73535 77.0376358 2.83219934 15-Dec-08 14:01:00 173.4000702 6763.06641 76.9452362 2.83221841 15-Dec-08 14:02:00 173.204422 6786.04492 77.0992355 2.83223748 15-Dec-08 14:03:00 173.8883972 6801.61377 77.2532272 2.83225679 15-Dec-08 14:04:00 173.1139069 6729.26465 77.4072189 2.83227587 15-Dec-08 14:05:00 172.2709961 6723.43213 77.2452927 2.83229494 15-Dec-08 14:06:00 172.7203217 6765.58496 77.3986511 2.83231401 15-Dec-08 14:07:00 172.6657867 6798.54297 77.5520172 2.83233309 15-Dec-08 14:08:00 173.322464 6785.52588 77.7053833 2.83235216 15-Dec-08 14:09:00 173.4530334 6775.98145 77.7218323 2.83237147 15-Dec-08 14:10:00 173.6880035 6783.7998 77.5540771 2.83239055 15-Dec-08 14:11:00 174.091156 6787.2002 77.7582855 2.83240962 15-Dec-08 14:12:00 173.09935 6773.81641 77.9624939 2.83242869 15-Dec-08 14:13:00 173.7175751 6792.78223 78.1258621 2.83244777 15-Dec-08 14:14:00 172.6379242 6744.61035 78.0110474 2.83246684 15-Dec-08 14:15:00 173.6240692 6766.06104 77.7100754 2.83248615 15-Dec-08 14:16:00 173.8586578 6773.76123 77.2018967 2.83250523 15-Dec-08 14:17:00 173.2462921 6777.93555 77.3045578 2.8325243 15-Dec-08 14:18:00 173.2026062 6764.48047 77.4072266 2.83254337 15-Dec-08 14:19:00 172.9852905 6748.20361 77.2121658 2.83256245 15-Dec-08 14:20:00 172.7679749 6718.35596 77.4790878 2.83258152 15-Dec-08 14:21:00 172.5506592 6707.20459 77.5021744 2.83260083 15-Dec-08 14:22:00 172.0380859 6724.28906 77.5788574 2.83261991 15-Dec-08 14:23:00 173.2303772 6741.37354 77.6555405 2.83263898 15-Dec-08 14:24:00 173.6371155 6755.70264 77.7322235 2.83265805 15-Dec-08 14:25:00 173.4345093 6756.25244 77.8088989 2.83267713 15-Dec-08 14:26:00 173.5578308 6760.07715 77.5201492 2.8326962 15-Dec-08 14:27:00 173.7319336 6775.29199 77.5713348 2.83271551 15-Dec-08 14:28:00 173.9060364 6762.2749 77.6481781 2.83273458 15-Dec-08 14:29:00 173.488266 6744.17041 77.7250137 2.83275366 15-Dec-08 14:30:00 172.3103943 6710.54004 77.801857 2.83277273 15-Dec-08 14:31:00 171.9741211 6740.14893 77.8786926 2.83279181



## Page 2 of 2

## PI Ops Data Run 4

Plant Information Source: polk-1pisrv Start Time: 12/16/2008 9:05

End Time: 12/16/2008 10:15 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 173.0486274 6747.95193 66.4618365 2.88816644 16-Dec-08 09:05:00 173.2203217 6734.36768 64.3788071 2.88393021 16-Dec-08 09:06:00 173.1763306 6736.12793 64.3984833 2.88405108 16-Dec-08 09:07:00 172.985733 6728.86768 64.6294785 2.8841722 16-Dec-08 09:08:00 173.3718414 6750.81006 64.860466 2.88429332 16-Dec-08 09:09:00 173.1413879 6742.92676 65.0914612 2.8844142 16-Dec-08 09:10:00 172.4518585 6727.82275 64.940033 2.88453531 16-Dec-08 09:11:00 172.0778351 6713.98633 65.2648315 2.88465643 16-Dec-08 09:12:00 173.492691 6739.89209 65.3086243 2.88477731 16-Dec-08 09:13:00 173.3335876 6741.35889 65.352417 2.88489842 16-Dec-08 09:14:00 173.1744995 6740.3667 65.3962097 2.88501954 16-Dec-08 09:15:00 173.0223846 6733.15527 65.4400024 2.88514042 16-Dec-08 09:16:00 172.9470673 6725.94385 65.4837952 2.88526154 16-Dec-08 09:17:00 172.8621826 6728.04834 65.5275879 2.88538265 16-Dec-08 09:18:00 172.6532745 6748.9375 65.6014175 2.88550353 16-Dec-08 09:19:00 172.9054413 6741.6709 65.9026566 2.88562465 16-Dec-08 09:20:00 172.4043121 6709.43896 66.1632843 2.88574576 16-Dec-08 09:21:00 172.6395416 6719.57813 65.8860855 2.88586664 16-Dec-08 09:22:00 172.1661987 6718.12402 66.1632309 2.88598776 16-Dec-08 09:23:00 173.2667084 6731.8374 65.8732376 2.88610888 16-Dec-08 09:24:00 173.8261108 6740.1001 66.0259781 2.88622975 16-Dec-08 09:25:00 172.5392914 6711.76904 66.1787262 2.88635087 16-Dec-08 09:26:00 172.6138 6731.31152 66.0361633 2.88647199 16-Dec-08 09:27:00 173.6668549 6750.854 65.8834152 2.88659286 16-Dec-08 09:28:00 174.0005188 6760.01074 66.4353333 2.88671398 16-Dec-08 09:29:00 172.643219 6738.00977 66.215126 2.8868351 16-Dec-08 09:30:00 172.0358124 6723.28174 66.4609985 2.88695598 16-Dec-08 09:31:00 172.2720032 6728.42725 66.4456024 2.88707709 16-Dec-08 09:32:00 172.4405975 6724.63818 66.2360001 2.88719821 16-Dec-08 09:33:00 172.5126495 6726.09277 66.496933 2.88731909 16-Dec-08 09:34:00 172.2001495 6712.11035 66.183815 2.8874402 16-Dec-08 09:35:00 172.4937592 6736.43555 66.3788757 2.88756132 16-Dec-08 09:36:00 173.1445923 6740.68799 66.2248764 2.8876822 16-Dec-08 09:37:00 173.7954407 6754.06592 66.2741547 2.88780332 16-Dec-08 09:38:00 173.6329193 6783.72852 66.3973541 2.88792443



## Page 1 of 2

## PI Ops Data Run 4

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 16-Dec-08 09:39:00 173.1658325 6776.94531 66.520546 2.88804531 16-Dec-08 09:40:00 173.1027985 6766.61084 66.6437378 2.88816643 16-Dec-08 09:41:00 173.2180634 6751.28369 66.7669296 2.88828754 16-Dec-08 09:42:00 173.4792328 6757.88428 66.5623093 2.88840842 16-Dec-08 09:43:00 173.3233795 6768.33447 66.665535 2.88852954 16-Dec-08 09:44:00 174.004364 6788.18408 66.7687607 2.88865066 16-Dec-08 09:45:00 173.2510529 6789.12109 67.0884933 2.88877153 16-Dec-08 09:46:00 172.7871704 6771.07227 67.027298 2.88889265 16-Dec-08 09:47:00 172.8637085 6777.18359 66.9661026 2.88901377 16-Dec-08 09:48:00 173.3022766 6783.29492 66.9049072 2.88913465 16-Dec-08 09:49:00 173.2372437 6770.83691 66.8437119 2.88925576 16-Dec-08 09:50:00 172.6357117 6725.67725 66.9509506 2.88937688 16-Dec-08 09:51:00 173.1499329 6744.81787 66.943512 2.88949776 16-Dec-08 09:52:00 173.1033936 6738.31543 67.0590057 2.88961887 16-Dec-08 09:53:00 174.0241699 6762.89551 66.905014 2.88973999 16-Dec-08 09:54:00 173.510849 6758.64209 66.9262085 2.88986087 16-Dec-08 09:55:00 172.7311249 6740.35693 67.0135803 2.88998199 16-Dec-08 09:56:00 172.7129669 6747.25781 67.0205078 2.8901031 16-Dec-08 09:57:00 172.4082642 6741.22852 66.9075775 2.89022398 16-Dec-08 09:58:00 173.641922 6758.50195 67.0322647 2.8903451 16-Dec-08 09:59:00 173.7409973 6772.51465 66.8645096 2.89046621 16-Dec-08 10:00:00 173.6847076 6769.65479 67.068718 2.89058709 16-Dec-08 10:01:00 172.9918823 6756.0332 67.2729263 2.89070821 16-Dec-08 10:02:00 173.6323242 6761.01904 67.4240189 2.89082932 16-Dec-08 10:03:00 172.5830841 6739.93506 67.3626175 2.8909502 16-Dec-08 10:04:00 173.4081573 6757.05322 67.3012238 2.89107132 16-Dec-08 10:05:00 173.6329193 6769.95996 67.2398224 2.89119244 16-Dec-08 10:06:00 173.0835876 6738.47461 67.1784286 2.89131355 16-Dec-08 10:07:00 172.534256 6746.51953 67.1539688 2.89143443 16-Dec-08 10:08:00 174.0201569 6806.93799 67.410202 2.89155555 16-Dec-08 10:09:00 173.8599701 6786.28174 67.4154205 2.89167666 16-Dec-08 10:10:00 173.6718903 6765.625 67.4414291 2.89179754 16-Dec-08 10:11:00 173.4837952 6754.48633 67.5440903 2.89191866 16-Dec-08 10:12:00 172.9342957 6759.54639 67.6467514 2.89203978 16-Dec-08 10:13:00 172.351944 6742.70361 67.7494125 2.89216065 16-Dec-08 10:14:00 171.7695923 6741.05322 67.9098511 2.89228177 16-Dec-08 10:15:00 172.3046112 6743.55908 67.7545853 2.89240289



## Page 2 of 2

## PI Ops Data Run 5

Plant Information Source: polk-1pisrv Start Time: 12/16/2008 10:49

End Time: 12/16/2008 11:57 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 173.0510785 6763.43727 69.452557 2.90063334 16-Dec-08 10:49:00 173.7049713 6757.02881 68.036911 2.89651799 16-Dec-08 10:50:00 173.1466217 6734.66113 68.3518295 2.89663911 16-Dec-08 10:51:00 172.6369171 6734.47754 68.2497253 2.89676023 16-Dec-08 10:52:00 172.5648804 6729.94336 68.1476212 2.8968811 16-Dec-08 10:53:00 172.4477997 6720.58057 68.1138611 2.89700222 16-Dec-08 10:54:00 171.8087769 6730.84766 68.1035995 2.89712334 16-Dec-08 10:55:00 173.230072 6736.8125 68.3667068 2.89724422 16-Dec-08 10:56:00 173.0995026 6730.94531 68.2900238 2.89736533 16-Dec-08 10:57:00 172.9689178 6741.70117 68.2133408 2.89748645 16-Dec-08 10:58:00 172.3029785 6781.64502 68.1366577 2.89760733 16-Dec-08 10:59:00 173.2269287 6772.03809 68.0727997 2.89772844 16-Dec-08 11:00:00 173.6373901 6765.41357 68.3807831 2.89784956 16-Dec-08 11:01:00 174.005127 6792.86523 68.6887741 2.89797044 16-Dec-08 11:02:00 174.5043182 6799.31885 68.5866699 2.89809155 16-Dec-08 11:03:00 174.526474 6792.10742 68.4845657 2.89821267 16-Dec-08 11:04:00 172.8135071 6787.4873 68.3824615 2.89833355 16-Dec-08 11:05:00 172.6556549 6761.13525 68.6631088 2.89845467 16-Dec-08 11:06:00 172.4679565 6760.39355 68.5476151 2.89857578 16-Dec-08 11:07:00 172.0785675 6768.70508 68.3936234 2.89869666 16-Dec-08 11:08:00 173.440506 6777.0166 68.5553131 2.89881778 16-Dec-08 11:09:00 173.3253021 6777.00049 68.4013214 2.89893889 16-Dec-08 11:10:00 172.5247955 6754.08301 68.8889618 2.89905977 16-Dec-08 11:11:00 173.5427246 6744.02393 68.4904633 2.89918089 16-Dec-08 11:12:00 173.3732605 6762.52881 68.4463577 2.89930201 16-Dec-08 11:13:00 173.1060944 6762.34521 68.615715 2.89942288 16-Dec-08 11:14:00 173.0025482 6769.23193 68.6066437 2.899544 16-Dec-08 11:15:00 173.8223419 6784.50391 68.4629211 2.89966512 16-Dec-08 11:16:00 173.8727722 6772.25781 68.4484329 2.899786 16-Dec-08 11:17:00 173.2303925 6775.55811 68.5499878 2.89990711 16-Dec-08 11:18:00 173.140625 6778.8584 68.651535 2.90002823 16-Dec-08 11:19:00 172.9582672 6774.14014 68.4904633 2.90014911 16-Dec-08 11:20:00 172.7511292 6754.99951 68.498848 2.90027022 16-Dec-08 11:21:00 172.7921143 6756.83301 68.5594406 2.90039134 16-Dec-08 11:22:00 172.3786163 6758.6665 68.8657532 2.90051222



## Page 1 of 2

## PI Ops Data Run 5

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 16-Dec-08 11:23:00 172.8485413 6768.71338 69.1720657 2.90063334 16-Dec-08 11:24:00 174.1778259 6797.53467 69.1480103 2.90075445 16-Dec-08 11:25:00 174.1241608 6797.3877 69.2752304 2.90087533 16-Dec-08 11:26:00 173.0505676 6755.875 69.1982346 2.90099645 16-Dec-08 11:27:00 172.5822906 6759.55273 69.1212387 2.90111756 16-Dec-08 11:28:00 172.471756 6808.5957 69.0442429 2.90123844 16-Dec-08 11:29:00 173.025589 6814.55469 69.1837006 2.90135956 16-Dec-08 11:30:00 173.0989075 6791.04785 69.0939102 2.90148067 16-Dec-08 11:31:00 172.2659912 6753.31299 69.3239594 2.90160155 16-Dec-08 11:32:00 172.5551147 6766.17139 69.5540085 2.90172267 16-Dec-08 11:33:00 173.4714203 6788.44092 69.7840576 2.90184379 16-Dec-08 11:34:00 172.9902496 6772.01367 69.8421021 2.90196466 16-Dec-08 11:35:00 172.3163452 6751.33643 69.971199 2.90208578 16-Dec-08 11:36:00 173.1473694 6765.55762 70.0710068 2.9022069 16-Dec-08 11:37:00 172.5144196 6779.7793 70.1708145 2.90232778 16-Dec-08 11:38:00 173.3349915 6785.31787 70.1720276 2.90244889 16-Dec-08 11:39:00 172.5695343 6758.64209 70.0073624 2.90257001 16-Dec-08 11:40:00 172.4838257 6739.74561 70.3125 2.90269089 16-Dec-08 11:41:00 173.0353851 6773.43115 70.61763 2.902812 16-Dec-08 11:42:00 173.1161041 6769.95898 70.819725 2.90293312 16-Dec-08 11:43:00 173.1968231 6771.10254 70.8872223 2.903054 16-Dec-08 11:44:00 173.2775421 6751.70752 70.9893341 2.90317512 16-Dec-08 11:45:00 173.3582611 6755.02393 71.0914383 2.90329623 16-Dec-08 11:46:00 174.0246582 6754.33936 71.1589432 2.90341711 16-Dec-08 11:47:00 172.9022827 6775.26465 71.1799011 2.90353823 16-Dec-08 11:48:00 171.7495728 6760.96436 71.07724 2.90365934 16-Dec-08 11:49:00 173.0628357 6746.66357 70.9745712 2.90378022 16-Dec-08 11:50:00 172.5990906 6740.6748 70.8719101 2.90390134 16-Dec-08 11:51:00 173.0673828 6747.94629 71.1850357 2.90402246 16-Dec-08 11:52:00 172.8671722 6737.07617 71.7804718 2.90414333 16-Dec-08 11:53:00 173.1305695 6750.94238 71.8112717 2.90426445 16-Dec-08 11:54:00 172.6837921 6755.92822 71.8112717 2.90438557 16-Dec-08 11:55:00 173.135376 6746.27246 71.8112717 2.90450644 16-Dec-08 11:56:00 173.8017731 6750.30615 72.4182358 2.90462756 16-Dec-08 11:57:00 173.3980408 6735.83447 72.5524521 2.90474868



## Page 2 of 2

## PI Ops Data Run 6

Plant Information Source: polk-1pisrv Start Time: 12/16/2008 12:13

End Time: 12/16/2008 13:20 Time Interval: 1m

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O Run Average: 172.9492529 6753.67327 75.5018634 2.91073994 16-Dec-08 12:13:00 172.9847107 6750.60742 73.9151382 2.90668511 16-Dec-08 12:14:00 172.5476227 6748.65625 73.9048691 2.90680623 16-Dec-08 12:15:00 172.252243 6750.57178 73.9057159 2.90692735 16-Dec-08 12:16:00 172.6333008 6740.85498 74.2153931 2.90704823 16-Dec-08 12:17:00 172.9078369 6751.55762 74.5250778 2.90716934 16-Dec-08 12:18:00 173.0861511 6805.77246 74.2792664 2.90729046 16-Dec-08 12:19:00 173.3182068 6776.62158 73.8761215 2.90741134 16-Dec-08 12:20:00 172.8448029 6751.23486 74.377121 2.90753245 16-Dec-08 12:21:00 172.7679901 6747.07129 74.377121 2.90765357 16-Dec-08 12:22:00 173.7817993 6779.8584 74.289856 2.90777445 16-Dec-08 12:23:00 173.961319 6782.26367 74.4797821 2.90789557 16-Dec-08 12:24:00 171.736969 6753.87354 74.7877655 2.90801668 16-Dec-08 12:25:00 171.9862976 6755.94678 74.910965 2.90813756 16-Dec-08 12:26:00 171.9628601 6734.44287 74.777504 2.90825868 16-Dec-08 12:27:00 172.6670837 6747.23145 74.922554 2.90837979 16-Dec-08 12:28:00 172.8201752 6754 74.7141266 2.90850067 16-Dec-08 12:29:00 173.5559235 6750.03223 74.8165131 2.90862179 16-Dec-08 12:30:00 174.0767365 6755.6748 74.9188919 2.9087429 16-Dec-08 12:31:00 173.7365875 6766.4917 75.0212708 2.90886378 16-Dec-08 12:32:00 173.9820557 6764.31934 75.1236572 2.9089849 16-Dec-08 12:33:00 171.7698517 6721.60303 75.2260361 2.90910602 16-Dec-08 12:34:00 172.0490112 6716.95557 75.3514099 2.90922689 16-Dec-08 12:35:00 172.9187927 6726.23975 75.5601501 2.90934801 16-Dec-08 12:36:00 172.2627563 6718.97949 75.0118637 2.90946913 16-Dec-08 12:37:00 172.8430023 6743.80371 75.1139679 2.90959001 16-Dec-08 12:38:00 173.3803253 6773.51709 75.2160721 2.90971112 16-Dec-08 12:39:00 173.8846283 6763.72656 75.3112564 2.90983224 16-Dec-08 12:40:00 172.2249146 6736.59229 75.3164749 2.90995312 16-Dec-08 12:41:00 172.5871124 6731.75195 75.1637344 2.91007423 16-Dec-08 12:42:00 173.2480927 6746.77051 75.010994 2.91019535 16-Dec-08 12:43:00 173.3882751 6765.81299 75.3886566 2.91031623 16-Dec-08 12:44:00 173.0418701 6764.67773 75.7942429 2.91043735 16-Dec-08 12:45:00 173.1178284 6752.67725 76.1998215 2.91055846 16-Dec-08 12:46:00 173.3208313 6749.20605 76.247139 2.91067934



## Page 1 of 2

## PI Ops Data Run 6

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202 

### Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator Tag Units: Mwe KCFH oF % H2O 16-Dec-08 12:47:00 173.5238495 6766.23193 76.247139 2.91080046 16-Dec-08 12:48:00 173.2874146 6803.18115 75.934021 2.91092157 16-Dec-08 12:49:00 173.1622314 6786.30176 76.162056 2.91104245 16-Dec-08 12:50:00 173.1442261 6751.32031 76.0599518 2.91116357 16-Dec-08 12:51:00 172.7897186 6742.74023 75.9578476 2.91128469 16-Dec-08 12:52:00 172.8140259 6753.36182 76.0122986 2.91140556 16-Dec-08 12:53:00 173.3993835 6754.61328 76.1144028 2.91152668 16-Dec-08 12:54:00 173.0188904 6747.24902 76.216507 2.9116478 16-Dec-08 12:55:00 172.7127228 6739.88477 76.0279541 2.91176867 16-Dec-08 12:56:00 172.4065399 6732.52051 76.1427689 2.91188979 16-Dec-08 12:57:00 172.6683502 6743.17969 75.9900284 2.91201091 16-Dec-08 12:58:00 173.038269 6763.54443 76.1290817 2.91213179 16-Dec-08 12:59:00 173.074585 6762.18652 75.8672867 2.9122529 16-Dec-08 13:00:00 172.7962799 6731.80762 75.6821594 2.91237402 16-Dec-08 13:01:00 172.7234955 6752.87891 75.7842636 2.9124949 16-Dec-08 13:02:00 173.2864532 6767.37158 75.8863678 2.91261601 16-Dec-08 13:03:00 172.9555511 6760.64404 76.2572403 2.91273713 16-Dec-08 13:04:00 172.2033081 6747.03027 76.4826279 2.91285801 16-Dec-08 13:05:00 172.3134766 6721.06934 76.3273621 2.91297913 16-Dec-08 13:06:00 172.3649597 6725.10303 76.2214737 2.91310024 16-Dec-08 13:07:00 172.7298279 6743.46094 76.560257 2.91322112 16-Dec-08 13:08:00 173.5077972 6758.43652 76.560257 2.91334224 16-Dec-08 13:09:00 173.690918 6763.67773 76.1208801 2.91346335 16-Dec-08 13:10:00 173.4001312 6763.67773 75.9508438 2.91358423 16-Dec-08 13:11:00 172.609787 6779.93359 75.9947433 2.91370535 16-Dec-08 13:12:00 173.4750214 6776.80469 76.0386353 2.91382647 16-Dec-08 13:13:00 173.2748108 6747.94727 76.0825348 2.91394734 16-Dec-08 13:14:00 172.264389 6749.37695 76.1264267 2.91406846 16-Dec-08 13:15:00 172.713913 6761.39209 76.1703262 2.91418958 16-Dec-08 13:16:00 172.7949677 6746.26025 76.2142181 2.91431046 16-Dec-08 13:17:00 172.5339508 6758.93555 76.4883957 2.91443157 16-Dec-08 13:18:00 174.4347076 6767.69873 76.1804123 2.91455269 16-Dec-08 13:19:00 173.0819092 6760.73193 75.9650726 2.91467357 16-Dec-08 13:20:00 172.705368 6739.83105 76.1203384 2.91479468



## Page 2 of 2

## APPENDIX E

FUEL ANALYSISDate/time12/15/08 9:46 12/15/08 11:44Date/time12/16/08 8:00 12/15/08 11:04 12/15/08 12:57ELEMENT Pi Tag CAL. GAS MS Actual MS Normalized Adjustment Raw Data Adjusted DataNormalized &Adjusted Raw Data Adjusted DataNormalized& AdjustedH2 1ASHYI01536.00 36.20 36.22 1.006 33.35 33.56 32.68 33.37 33.58 32.72N2 1ASHYI0163.15 3.13 3.13 0.994 3.54 3.52 3.47 3.45 3.43 3.38CH4 1ASHYI0180.0336 0.0328 0.0328 0.977 0.0271 0.03 0.03 0.0275 0.03 0.03CO 1ASHYI02144.14 43.90 43.93 0.995 45.71 45.49 44.79 45.67 45.46 44.78H2S 1ASHYI0190.6010 0.6216 0.6220 1.00 0.0207 0.02 0.02 0.0223 0.02 0.02CO2 1ASHYI02215.00 15.00 15.01 1.001 15.70 15.71 15.39 15.74 15.75 15.44COS 1ASHYI0200.0300 0.0204 0.0204 1.00 0.0100 0.01 0.01 0.0101 0.01 0.01AR 1ASHYI0171.05 1.03 1.03 0.982 0.81 0.80 0.80 0.81 0.80 0.80Subtotal (Dry)100.00 99.93 100.00 1.000 99.17 99.13 97.17 99.11 99.07 97.17H2O 1TSYAI2022.83 2.83 2.83 2.83 2.83 2.83Total (Moist)100.00 100.00Mole Wt (Moist)21.79 21.79Flow (KSCFH) 1TSYFI1006760 6622 6768 6630Mole Wt (Dry)21.90 21.90HHV-Dry (BTU/SCF)257.3 257.4HHV-Moist (BTU/SCF)250.0 250.1HHV (MMBTU/Hr)1656 1658LHV (BTU/SCF)233.7 233.8LHV (MMTU/Hr)1548 1550SO2 (Lb/Hr) from MS336 355SO2 (Lb/Hr) from CEM 1FGOFYI906320 328HHV TO CT 1tshai2001592 1595DRY GAS TO CT 1tshai2011589 1589Run 1CALIBRATION CHECK AND ADJUSTMENT FACTORSRun 212/15/08 13:23 12/16/08 9:05 12/16/08 10:49 12/16/08 12:1312/15/08 14:31 12/16/08 10:15 12/16/08 11:57 12/16/08 13:20Raw Data Adjusted DataNormalized& Adjusted Raw Data Adjusted DataNormalized& Adjusted Raw Data Adjusted DataNormalized& Adjusted Raw Data Adjusted DataNormalized& Adjusted33.37 33.58 32.78 32.99 33.19 32.38 32.97 33.18 32.31 32.92 33.13 32.323.42 3.40 3.36 3.35 3.34 3.29 3.41 3.39 3.34 3.28 3.26 3.220.0272 0.03 0.03 0.0282 0.03 0.03 0.0284 0.03 0.03 0.0279 0.03 0.0345.61 45.39 44.79 45.88 45.67 45.04 45.90 45.68 44.97 45.95 45.73 45.100.0223 0.02 0.02 0.0231 0.02 0.02 0.0223 0.02 0.02 0.0223 0.02 0.0215.66 15.67 15.38 15.83 15.84 15.54 15.93 15.94 15.61 15.86 15.87 15.570.0106 0.01 0.01 0.0110 0.01 0.01 0.0110 0.01 0.01 0.0111 0.01 0.010.82 0.80 0.80 0.82 0.81 0.81 0.82 0.81 0.81 0.83 0.82 0.8298.93 98.90 97.17 98.94 98.90 97.11 99.09 99.06 97.10 98.90 98.87 97.092.83 2.83 2.83 2.89 2.89 2.89 2.90 2.90 2.90 2.91 2.91 2.91100.00 100.00 100.00 100.0021.77 21.89 21.92 21.916761 6627 6748 6595 6764 6607 6754 659821.87 22.00 22.03 22.03257.7 257.3 256.9 257.4250.4 249.9 249.5 249.91659 1648 1648 1649234.0 233.7 233.3 233.71551 1541 1541 1542360 371 364 365328 336 328 3281595 1591 1596 15951591 1589 1591 1589Run 5 Run 6Run 3 Run 4

## APPENDIX F

CEMS DATA

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/15/2008 9:46 37.38 17.6 8.7 10.7 799 12/15/2008 9:47 37.51 17.8 8.6 10.7 799.2 12/15/2008 9:48 37.49 17.4 8.6 10.6 808.3 12/15/2008 9:49 37.28 17.1 8.7 10.6 809.4 12/15/2008 9:50 37.48 17.4 8.7 10.6 817.8 12/15/2008 9:51 37.9 17.4 8.7 10.6 814.3 12/15/2008 9:52 37.97 17.2 8.6 10.6 801.4 12/15/2008 9:53 38.28 17.3 8.6 10.7 800.1 12/15/2008 9:54 37.97 17.6 8.6 10.7 805.8 12/15/2008 9:55 38.11 17.6 8.6 10.6 803.6 12/15/2008 9:56 38.56 17.3 8.7 10.6 803.3 12/15/2008 9:57 38.36 17.6 8.7 10.7 814.3 12/15/2008 9:58 38.3 17.7 8.6 10.7 817.8 12/15/2008 9:59 38.6 17.7 8.7 10.6 809.6 12/15/2008 10:00 38.39 17.3 8.6 10.6 811.5 12/15/2008 10:01 38.23 17.4 8.7 10.6 814.1 12/15/2008 10:02 38.27 17.3 8.7 10.7 813.5 12/15/2008 10:03 38.55 17.5 8.7 10.6 808.8 12/15/2008 10:04 38.31 17.1 8.6 10.6 810 12/15/2008 10:05 38.82 17.1 8.7 10.6 803 12/15/2008 10:06 38.52 17.7 8.7 10.7 799 12/15/2008 10:07 38.34 17.6 8.7 10.6 817.4 12/15/2008 10:08 38.69 17 8.6 10.6 819.6 12/15/2008 10:09 38.43 16.8 8.7 10.6 816.2 12/15/2008 10:10 38.29 17 8.7 10.6 793.8 12/15/2008 10:11 38.18 17.2 8.7 10.6 788.2 12/15/2008 10:12 38.35 17.2 8.7 10.7 801.3 12/15/2008 10:13 38.46 17.7 8.7 10.7 808.5 12/15/2008 10:14 38.38 17.5 8.7 10.7 806.9 12/15/2008 10:15 38.6 17.5 8.7 10.7 806 12/15/2008 10:16 38.34 17.9 8.7 10.7 809.6 12/15/2008 10:17 38.52 18.4 8.7 10.7 813.1 12/15/2008 10:18 38.84 17.8 8.7 10.7 821.2 12/15/2008 10:19 38.72 17.8 8.7 10.7 810.2 12/15/2008 10:20 38.55 17.8 8.7 10.7 821.6 12/15/2008 10:21 38.67 18.3 8.7 10.7 810.8 12/15/2008 10:22 38.36 17.9 8.6 10.7 806.1 12/15/2008 10:23 38.79 18.1 8.7 10.7 805.4 12/15/2008 10:24 38.69 18.4 8.7 10.7 813.6 12/15/2008 10:25 38.51 18.2 8.7 10.7 816

Page 1 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/15/2008 10:26 38.64 18.1 8.7 10.7 811.9 12/15/2008 10:27 38.41 18.1 8.7 10.7 808.9 12/15/2008 10:28 38.89 18.2 8.7 10.7 807.2 12/15/2008 10:29 38.83 17.9 8.7 10.7 812.3 12/15/2008 10:30 38.61 17.8 8.7 10.7 811.9 12/15/2008 10:31 38.52 18.3 8.7 10.7 819.2 12/15/2008 10:32 38.78 18.6 8.7 10.7 813.4 12/15/2008 10:33 38.69 18.2 8.7 10.7 809.8 12/15/2008 10:34 38.92 18.2 8.7 10.7 808.3 12/15/2008 10:35 38.71 18.2 8.7 10.7 804.3 12/15/2008 10:36 38.87 18.6 8.7 10.7 802.8 12/15/2008 10:37 38.89 18.4 8.7 10.7 809.7 12/15/2008 10:38 39.14 18.3 8.7 10.7 814.8 12/15/2008 10:39 39.08 18 8.7 10.7 819.1 12/15/2008 10:40 38.78 18.4 8.7 10.7 819.9 12/15/2008 10:41 38.63 18.4 8.7 10.8 820.7 12/15/2008 10:42 38.62 18.7 8.7 10.7 812.6 12/15/2008 10:43 38.63 18.9 8.7 10.7 808.1 12/15/2008 10:44 38.86 18.4 8.7 10.7 812.2 12/15/2008 10:45 38.72 18.5 8.7 10.7 804.3 12/15/2008 10:46 38.92 18.6 8.7 10.7 809.5 12/15/2008 10:47 38.87 18.9 8.7 10.7 819.4 12/15/2008 10:48 38.84 18.4 8.6 10.7 814.7 12/15/2008 10:49 38.97 18.2 8.7 10.7 807.5 12/15/2008 10:50 38.77 18.4 8.7 10.8 816.1 12/15/2008 10:51 38.82 18.8 8.7 10.7 814.4 12/15/2008 10:52 38.69 18.3 8.7 10.7 813.7 12/15/2008 10:53 38.49 18.4 8.7 10.7 814.1 12/15/2008 10:54 38.76 18.4 8.7 10.7 817 12/15/2008 10:55 38.51 18.1 8.7 10.8 815.1 12/15/2008 10:56 39.02 18.4 8.7 10.7 815.5 12/15/2008 10:57 39.03 18.1 8.7 10.7 817.7 12/15/2008 10:58 39.04 18.1 8.7 10.7 818 12/15/2008 10:59 39.06 17.7 8.7 10.7 816.7 12/15/2008 11:00 38.78 18 8.6 10.7 821.2 12/15/2008 11:01 38.97 18 8.6 10.7 822.8 12/15/2008 11:02 38.92 18.5 8.7 10.8 817.3 12/15/2008 11:03 38.91 18.7 8.7 10.7 815.8 12/15/2008 11:04 39.03 18.3 8.7 10.7 814 12/15/2008 11:05 39.19 18.3 8.7 10.7 808.1

Page 2 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/15/2008 11:06 39.29 18.4 8.7 10.8 818.4 12/15/2008 11:07 39.01 18.8 8.6 10.8 820 12/15/2008 11:08 38.94 18.6 8.7 10.7 815.5 12/15/2008 11:09 38.92 18.2 8.7 10.7 811.2 12/15/2008 11:10 38.64 18.4 8.6 10.7 809.6 12/15/2008 11:11 38.5 18.5 8.7 10.8 811.7 12/15/2008 11:12 38.78 18.5 8.6 10.8 819.2 12/15/2008 11:13 38.87 18.3 8.6 10.8 815.6 12/15/2008 11:14 38.93 18.7 8.6 10.7 809.1 12/15/2008 11:15 39.22 18.6 8.6 10.7 809 12/15/2008 11:16 39.06 18.5 8.7 10.7 809.9 12/15/2008 11:17 38.81 18.7 8.7 10.8 811.8 12/15/2008 11:18 38.82 18.6 8.7 10.7 816.5 12/15/2008 11:19 38.51 18.3 8.6 10.7 806.2 12/15/2008 11:20 38.57 18.3 8.6 10.7 811.7 12/15/2008 11:21 38.56 18.4 8.6 10.7 818.4 12/15/2008 11:22 38.69 18.7 8.6 10.7 814.7 12/15/2008 11:23 38.78 18.1 8.7 10.7 802.2 12/15/2008 11:24 38.99 18.2 8.7 10.7 801.8 12/15/2008 11:25 38.93 18.4 8.7 10.7 808.6 12/15/2008 11:26 38.94 18.4 8.7 10.7 813.9 12/15/2008 11:27 39.09 18.2 8.7 10.7 803.9 12/15/2008 11:28 39.25 18.2 8.7 10.7 809.9 12/15/2008 11:29 39.27 17.6 8.7 10.7 818.5 12/15/2008 11:30 39.34 18 8.7 10.7 824.4 12/15/2008 11:31 39.5 18.4 8.7 10.7 826.5 12/15/2008 11:32 39.34 18.6 8.6 10.8 819.3 12/15/2008 11:33 39.4 18.6 8.6 10.8 820.2 12/15/2008 11:34 39.54 18.3 8.6 10.7 818.4 12/15/2008 11:35 39.68 18.6 8.6 10.8 818.7 12/15/2008 11:36 39.31 18.8 8.7 10.7 815 12/15/2008 11:37 38.86 18.5 8.6 10.8 817.2 12/15/2008 11:38 39.19 18.6 8.6 10.7 808.6 12/15/2008 11:39 39.03 18.1 8.6 10.7 813.4 12/15/2008 11:40 38.57 18.3 8.6 10.8 819.8 12/15/2008 11:41 38.52 18.4 8.6 10.8 818.2 12/15/2008 11:42 38.83 18.8 8.7 10.7 816.1 12/15/2008 11:43 38.82 18.9 8.7 10.8 819.5 12/15/2008 11:44 39.04 18.7 8.7 10.7 816.2 12/15/2008 11:45 39.2 18.4 8.7 10.7 810

Page 3 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/15/2008 11:46 39.22 18.7 8.7 10.7 814.4 12/15/2008 11:47 39.04 19.1 8.7 10.7 815.1 12/15/2008 11:48 39.16 18.6 8.6 10.7 805.1 12/15/2008 11:49 39.37 18.1 8.6 10.7 808.7 12/15/2008 11:50 39.04 18.4 8.7 10.7 816 12/15/2008 11:51 39.27 18.8 8.6 10.8 819.6 12/15/2008 11:52 39 18.4 8.6 10.7 819.8 12/15/2008 11:53 39.13 18.3 8.7 10.7 814.6 12/15/2008 11:54 38.78 18.5 8.7 10.8 820.5 12/15/2008 11:55 38.64 18.7 8.6 10.8 822.3 12/15/2008 11:56 38.71 18.6 8.6 10.7 820.2 12/15/2008 11:57 38.99 18.4 8.7 10.7 815.8 12/15/2008 11:58 38.99 18.5 8.7 10.7 813.6 12/15/2008 11:59 38.98 18.3 8.6 10.7 814.6 12/15/2008 12:00 38.62 18.5 8.6 10.7 816.4 12/15/2008 12:01 39.12 18.3 8.7 10.7 814.9 12/15/2008 12:02 39.02 18.4 8.7 10.7 815.4 12/15/2008 12:03 39.2 18.6 8.7 10.8 817.5 12/15/2008 12:04 39.01 18.7 8.6 10.8 815.8 12/15/2008 12:05 39.19 18.6 8.6 10.7 814.5 12/15/2008 12:06 39.28 18.3 8.6 10.7 818.5 12/15/2008 12:07 39.04 18.4 8.6 10.8 810.8 12/15/2008 12:08 39.21 18.7 8.7 10.7 815 12/15/2008 12:09 39.11 18.7 8.7 10.7 814.5 12/15/2008 12:10 39.21 18.3 8.7 10.7 818.8 12/15/2008 12:11 39.51 18.4 8.7 10.8 820.6 12/15/2008 12:12 39.06 18.5 8.7 10.8 829.3 12/15/2008 12:13 39.25 18.7 8.7 10.7 819.5 12/15/2008 12:14 39.19 18.4 8.7 10.7 825.6 12/15/2008 12:15 39.48 18.3 8.7 10.7 814.7 12/15/2008 12:16 39.72 18.3 8.7 10.8 810.8 12/15/2008 12:17 39.18 18.8 8.7 10.7 813.2 12/15/2008 12:18 39.41 18.4 8.7 10.7 822.1 12/15/2008 12:19 39.17 17.8 8.7 10.7 826.2 12/15/2008 12:20 38.86 17.9 8.6 10.7 819.6 12/15/2008 12:21 39.44 18.4 8.7 10.8 814.7 12/15/2008 12:22 39.18 19 8.7 10.7 822.3 12/15/2008 12:23 39.14 18.5 8.6 10.7 808.5 12/15/2008 12:24 39.27 18.4 8.6 10.8 817.4 12/15/2008 12:25 39.54 18.6 8.7 10.8 820.9

Page 4 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/15/2008 12:26 35.61 14.1 4.9 10.8 813.9 12/15/2008 12:27 2.84 0.1 0.6 10.7 817.2 12/15/2008 12:28 19.31 11.4 7.6 10.7 821.4 12/15/2008 12:29 37.84 17.6 8.6 10.7 822.9 12/15/2008 12:30 39.07 18.4 8.6 10.7 813 12/15/2008 12:31 39.04 18.6 8.6 10.8 813.6 12/15/2008 12:32 38.81 18.8 8.6 10.8 824.8 12/15/2008 12:33 39.17 18.9 8.6 10.7 817.7 12/15/2008 12:34 39.19 18.6 8.6 10.7 823.5 12/15/2008 12:35 38.91 18.6 8.6 10.7 821 12/15/2008 12:36 38.73 18.7 8.6 10.8 823.1 12/15/2008 12:37 38.95 18.8 8.6 10.7 817.6 12/15/2008 12:38 38.99 18.4 8.6 10.7 813.6 12/15/2008 12:39 39.05 18 8.6 10.7 807.3 12/15/2008 12:40 39.04 17.9 8.6 10.7 813.5 12/15/2008 12:41 39.19 18.1 8.6 10.7 813.7 12/15/2008 12:42 38.9 18 8.6 10.7 803.6 12/15/2008 12:43 38.86 18 8.6 10.7 806.3 12/15/2008 12:44 38.99 18 8.6 10.7 815.6 12/15/2008 12:45 38.87 18.2 8.6 10.7 813.9 12/15/2008 12:46 38.92 18.1 8.6 10.7 820 12/15/2008 12:47 38.97 17.6 8.6 10.7 821.8 12/15/2008 12:48 39.49 17.6 8.6 10.6 825.9 12/15/2008 12:49 39.44 17.2 8.6 10.7 810 12/15/2008 12:50 39.37 17.9 8.6 10.7 818.6 12/15/2008 12:51 39.61 18.1 8.6 10.7 820 12/15/2008 12:52 39.73 18.1 8.6 10.7 820.8 12/15/2008 12:53 39.42 18.4 8.6 10.7 817.1 12/15/2008 12:54 39.81 18.3 8.6 10.7 810.2 12/15/2008 12:55 39.28 18.6 8.6 10.7 810.2 12/15/2008 12:56 39.22 18.4 8.6 10.7 813.7 12/15/2008 12:57 39.59 18.2 8.6 10.7 811 12/15/2008 12:58 39.6 18.3 8.6 10.7 814.6 12/15/2008 12:59 39.76 18.5 8.6 10.7 817.4 12/15/2008 13:00 39.38 18.4 8.6 10.7 820.4 12/15/2008 13:01 39.42 18.2 8.6 10.7 818.8 12/15/2008 13:02 39.85 18.3 8.6 10.7 820.7 12/15/2008 13:03 39.99 18.3 8.6 10.7 820.7 12/15/2008 13:04 39.73 18.3 8.6 10.7 810.9 12/15/2008 13:05 39.96 18.6 8.6 10.7 813.1

Page 5 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/15/2008 13:06 39.45 18.4 8.6 10.7 811.8 12/15/2008 13:07 39.69 18.2 8.6 10.7 813.6 12/15/2008 13:08 39.83 18.4 8.6 10.7 813.9 12/15/2008 13:09 39.64 18.5 8.6 10.7 821.5 12/15/2008 13:10 39.36 18.1 8.6 10.7 826.1 12/15/2008 13:11 39.02 18.4 8.6 10.7 819.7 12/15/2008 13:12 38.83 18.6 8.6 10.7 818.4 12/15/2008 13:13 38.74 18.6 8.6 10.7 821.5 12/15/2008 13:14 38.4 18.6 8.6 10.7 809.2 12/15/2008 13:15 38.73 18.3 8.6 10.7 824 12/15/2008 13:16 38.71 18.3 8.6 10.7 799.4 12/15/2008 13:17 38.53 18.5 8.6 10.8 804.3 12/15/2008 13:18 38.42 18.8 8.6 10.7 817.6 12/15/2008 13:19 38.42 18 8.6 10.7 817.4 12/15/2008 13:20 38.2 18.3 8.6 10.7 828.3 12/15/2008 13:21 37.85 18.7 8.6 10.7 825.6 12/15/2008 13:22 37.95 18.8 8.6 10.7 823.5 12/15/2008 13:23 37.7 18.6 8.6 10.7 813.4 12/15/2008 13:24 38.06 18.6 8.6 10.7 822.5 12/15/2008 13:25 38.15 18.7 8.6 10.7 819.5 12/15/2008 13:26 38.49 18.9 8.6 10.7 820.4 12/15/2008 13:27 38.74 18.8 8.6 10.7 831.1 12/15/2008 13:28 39.02 18.6 8.6 10.7 808 12/15/2008 13:29 38.87 18.4 8.6 10.7 809 12/15/2008 13:30 38.98 18.7 8.6 10.7 818.9 12/15/2008 13:31 39.29 18.8 8.6 10.7 824.5 12/15/2008 13:32 39.29 18.5 8.6 10.7 817.4 12/15/2008 13:33 39.5 18.6 8.6 10.8 813.9 12/15/2008 13:34 39.39 18.9 8.6 10.8 813 12/15/2008 13:35 39.2 18.6 8.6 10.7 815.8 12/15/2008 13:36 39.56 18.4 8.6 10.7 827.1 12/15/2008 13:37 39.73 18.7 8.6 10.8 821.7 12/15/2008 13:38 39.65 18.6 8.6 10.7 817.1 12/15/2008 13:39 39.27 18 8.6 10.7 820.1 12/15/2008 13:40 39.35 18.1 8.6 10.7 810.7 12/15/2008 13:41 39.15 18.4 8.6 10.7 815.2 12/15/2008 13:42 39.15 18.8 8.6 10.8 815.1 12/15/2008 13:43 39.47 18.6 8.6 10.7 814.7 12/15/2008 13:44 39.65 18.4 8.6 10.7 804.5 12/15/2008 13:45 39.77 18.4 8.6 10.7 811.3

Page 6 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/15/2008 13:46 39.66 18.5 8.6 10.8 816.3 12/15/2008 13:47 39.87 18.8 8.6 10.8 804.6 12/15/2008 13:48 39.63 18.6 8.6 10.7 793.3 12/15/2008 13:49 39.46 18.1 8.6 10.7 806.9 12/15/2008 13:50 38.94 18.5 8.6 10.8 819.5 12/15/2008 13:51 38.67 18.7 8.6 10.7 814 12/15/2008 13:52 39.55 18.8 8.6 10.8 816 12/15/2008 13:53 38.91 19 8.6 10.7 818.8 12/15/2008 13:54 39.31 18.7 8.6 10.8 821.2 12/15/2008 13:55 39.34 18.7 8.6 10.7 823.7 12/15/2008 13:56 39.43 18.7 8.6 10.7 815 12/15/2008 13:57 38.85 18.9 8.6 10.8 824.6 12/15/2008 13:58 38.94 18.8 8.6 10.7 812.9 12/15/2008 13:59 39.19 18 8.6 10.7 816.5 12/15/2008 14:00 39.2 17.9 8.6 10.7 802.7 12/15/2008 14:01 39.16 18.2 8.6 10.7 812.6 12/15/2008 14:02 39.23 18.6 8.6 10.7 815.5 12/15/2008 14:03 39.41 18.1 8.6 10.7 824.4 12/15/2008 14:04 39.56 18.2 8.6 10.7 834.1 12/15/2008 14:05 39.54 18.2 8.6 10.7 833.3 12/15/2008 14:06 39.69 18.1 8.6 10.8 813.2 12/15/2008 14:07 39.72 18.4 8.6 10.8 825.5 12/15/2008 14:08 39.69 18.6 8.6 10.7 814.3 12/15/2008 14:09 39.4 17.7 8.6 10.7 825.2 12/15/2008 14:10 39.01 18 8.6 10.7 813.4 12/15/2008 14:11 39.18 18.5 8.6 10.8 818 12/15/2008 14:12 39.3 18.8 8.6 10.8 818.2 12/15/2008 14:13 39.37 18.7 8.6 10.7 813.7 12/15/2008 14:14 39.83 18.6 8.6 10.7 826.4 12/15/2008 14:15 39.81 18.7 8.6 10.8 810.7 12/15/2008 14:16 39.84 18.7 8.6 10.8 817.5 12/15/2008 14:17 39.5 19 8.6 10.8 816.1 12/15/2008 14:18 39.54 18.7 8.6 10.7 824.4 12/15/2008 14:19 39.82 18.4 8.6 10.7 806.5 12/15/2008 14:20 39.32 18.4 8.6 10.8 818.4 12/15/2008 14:21 39.49 18.5 8.6 10.8 819.2 12/15/2008 14:22 39.66 18.7 8.6 10.8 821.6 12/15/2008 14:23 39.62 19.2 8.6 10.8 819.5 12/15/2008 14:24 39.42 18.9 8.6 10.8 813.8 12/15/2008 14:25 39.02 18.8 8.6 10.8 818.2

Page 7 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/15/2008 14:26 39.01 19 8.6 10.8 806.3 12/15/2008 14:27 39.07 19 8.6 10.7 822 12/15/2008 14:28 38.7 18.8 8.6 10.7 820.4 12/15/2008 14:29 38.68 18.7 8.6 10.8 823 12/15/2008 14:30 38.65 18.9 8.6 10.8 827 12/15/2008 14:31 38.89 18.8 8.6 10.8 820.4 A verages: 38.770 18.21 8.59 10.71 814.92

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 9:05 40.68 18.2 8.7 2.8 796.6 12/16/2008 9:06 40.64 18.4 8.7 8.2 805.6 12/16/2008 9:07 40.75 18.6 8.7 10.9 811.4 12/16/2008 9:08 40.4 18.2 8.7 10.9 809.6 12/16/2008 9:09 40.11 18.1 8.7 10.9 807 12/16/2008 9:10 40.25 18.1 8.7 10.9 807.3 12/16/2008 9:11 40.33 18.2 8.7 10.9 809.7 12/16/2008 9:12 39.98 17.8 8.6 10.9 810.6 12/16/2008 9:13 40.26 18.1 8.6 10.9 814.2 12/16/2008 9:14 40.28 18.4 8.6 10.9 813.1 12/16/2008 9:15 40.38 18.2 8.6 10.9 812.5 12/16/2008 9:16 40.15 17.9 8.6 10.9 815.3 12/16/2008 9:17 40.34 18.1 8.6 10.9 817.4 12/16/2008 9:18 40.44 18.1 8.6 10.9 816.8 12/16/2008 9:19 40.55 18.2 8.6 10.9 811.2 12/16/2008 9:20 40.65 17.8 8.6 10.9 812 12/16/2008 9:21 40.29 17.8 8.5 10.9 809.8 12/16/2008 9:22 40.32 18.2 8.5 10.9 805.7 12/16/2008 9:23 40.3 18.3 8.5 10.9 800.9 12/16/2008 9:24 40.2 18 8.5 10.9 805.1 12/16/2008 9:25 40.15 17.8 8.5 10.9 804.2 12/16/2008 9:26 40.32 17.7 8.5 10.9 807.5 12/16/2008 9:27 40.21 17.7 8.5 10.9 803.3 12/16/2008 9:28 40.46 18.2 8.5 10.9 808.5 12/16/2008 9:29 40.59 17.7 8.5 10.9 812.1 12/16/2008 9:30 40.15 17.3 8.5 10.9 811.5 12/16/2008 9:31 39.89 17.5 8.5 10.9 811.5 12/16/2008 9:32 40.4 17.9 8.5 10.9 800 12/16/2008 9:33 40.74 18.1 8.5 10.9 800.1 12/16/2008 9:34 41.04 17.8 8.5 10.9 803.1 12/16/2008 9:35 40.72 17.9 8.5 10.9 816.6

Page 8 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1

12/16/2008 9:36 40.64 18 8.5 10.9 807.9 12/16/2008 9:37 40.43 18.2 8.5 10.9 808.6 12/16/2008 9:38 40.75 18 8.5 10.8 805.7 12/16/2008 9:39 40.53 17.6 8.5 10.8 807.8 12/16/2008 9:40 40.47 16.9 8.5 10.8 805.5 12/16/2008 9:41 40.28 17.1 8.5 10.8 805.5 12/16/2008 9:42 40.58 17.6 8.5 10.8 797.6 12/16/2008 9:43 40.59 17.9 8.5 10.8 810.4 12/16/2008 9:44 40.72 17.5 8.5 10.8 806.1 12/16/2008 9:45 40.52 17.3 8.5 10.8 812.8 12/16/2008 9:46 40.95 17.5 8.5 10.8 811.2 12/16/2008 9:47 41.38 17.3 8.5 10.9 807.4 12/16/2008 9:48 41.17 17.6 8.5 10.9 803.6 12/16/2008 9:49 41.11 17.5 8.5 10.8 812.8 12/16/2008 9:50 40.92 17.2 8.5 10.8 816 12/16/2008 9:51 40.75 17.5 8.5 10.9 811.2 12/16/2008 9:52 40.95 17.9 8.5 10.9 810.7 12/16/2008 9:53 41.31 17.9 8.5 10.9 804.8 12/16/2008 9:54 40.65 17.7 8.5 10.9 802.6 12/16/2008 9:55 40.54 17.6 8.5 10.9 802.1 12/16/2008 9:56 40.62 17.6 8.5 10.9 810.6 12/16/2008 9:57 40.3 17.8 8.5 10.9 817.6 12/16/2008 9:58 40.19 17.9 8.5 10.8 814.8 12/16/2008 9:59 40.17 17.7 8.5 10.9 813.7 12/16/2008 10:00 40.19 17.7 8.5 10.9 808.8 12/16/2008 10:01 40.7 17.6 8.5 10.9 813 12/16/2008 10:02 40.66 17.7 8.6 10.8 805.1 12/16/2008 10:03 40.96 17.9 8.6 10.9 804.4 12/16/2008 10:04 40.77 17.9 8.5 10.9 813.8 12/16/2008 10:05 40.67 17.6 8.5 10.9 813.6 12/16/2008 10:06 41.25 17.7 8.6 10.9 816.6 12/16/2008 10:07 41.2 17.8 8.5 10.9 819.1 12/16/2008 10:08 41.49 17.9 8.5 10.8 815.4 12/16/2008 10:09 41.6 17.4 8.6 10.8 813.5 12/16/2008 10:10 41.11 17.2 8.6 10.8 814.6 12/16/2008 10:11 40.72 17.4 8.5 10.8 814.7 12/16/2008 10:12 40.92 17.7 8.5 10.9 817.8 12/16/2008 10:13 40.7 17.8 8.5 10.9 818.1 12/16/2008 10:14 40.61 17.7 8.5 10.9 814.4 12/16/2008 10:15 40.72 17.8 8.5 10.9 823.3

Page 9 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/16/2008 10:16 40.42 17.5 8.5 10.9 814.6 12/16/2008 10:17 40.64 17.7 8.5 10.9 816.1 12/16/2008 10:18 40.47 17.9 8.5 10.9 814.5 12/16/2008 10:19 40.21 17.7 8.4 10.8 810.4 12/16/2008 10:20 40.06 17.5 8.4 10.9 806.4 12/16/2008 10:21 39.69 17.4 8.4 10.9 812.7 12/16/2008 10:22 39.65 17.6 8.4 10.9 809.3 12/16/2008 10:23 39.76 17.9 8.4 10.9 806.7 12/16/2008 10:24 39.67 17.9 8.4 10.9 809.9 12/16/2008 10:25 39.39 17.7 8.4 10.9 813.7 12/16/2008 10:26 39.69 17.7 8.3 10.9 807.8 12/16/2008 10:27 39.36 17.9 8.4 10.9 804.6 12/16/2008 10:28 39.81 18.1 8.4 10.9 811.6 12/16/2008 10:29 39.86 17.7 8.4 10.9 813.9 12/16/2008 10:30 39.62 17.2 8.3 10.9 809.5 12/16/2008 10:31 39.06 17.7 8.3 10.9 817.3 12/16/2008 10:32 39.03 17.9 8.3 10.9 819.4 12/16/2008 10:33 38.89 17.8 8.3 10.9 814.5 12/16/2008 10:34 39.02 17.7 8.3 10.9 817.8 12/16/2008 10:35 38.91 17.8 8.3 10.9 817.9 12/16/2008 10:36 39.05 18 8.3 10.9 827.4 12/16/2008 10:37 39.34 18 8.3 10.9 821.5 12/16/2008 10:38 39.4 17.7 8.3 10.9 810.9 12/16/2008 10:39 38.85 17.7 8.3 10.9 799.9 12/16/2008 10:40 39.08 17.5 8.3 10.9 807.3 12/16/2008 10:41 39.34 17.8 8.3 10.9 809.4 12/16/2008 10:42 39.6 17.9 8.3 10.9 819.8 12/16/2008 10:43 39.41 17.8 8.3 10.9 811 12/16/2008 10:44 39.44 17.8 8.3 10.9 805.4 12/16/2008 10:45 39.5 17.7 8.3 10.9 811.2 12/16/2008 10:46 39.72 17.7 8.3 10.9 814 12/16/2008 10:47 39.51 18.1 8.4 10.9 815 12/16/2008 10:48 39.32 18.1 8.4 10.9 818 12/16/2008 10:49 39.36 17.8 8.4 10.9 816.2 12/16/2008 10:50 39.37 17.8 8.4 10.9 825.9 12/16/2008 10:51 39.19 17.8 8.4 10.9 818.2 12/16/2008 10:52 39.45 17.8 8.4 10.9 815.9 12/16/2008 10:53 39.41 17.9 8.4 10.9 811.9 12/16/2008 10:54 39.39 17.9 8.4 10.9 813.2 12/16/2008 10:55 39.55 17.9 8.4 10.9 812.6

Page 10 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/16/2008 10:56 39.35 17.8 8.4 10.8 807.9 12/16/2008 10:57 39.46 17.7 8.4 10.9 807 12/16/2008 10:58 38.94 17.6 8.4 10.8 809.8 12/16/2008 10:59 39.23 17.3 8.4 10.8 811.5 12/16/2008 11:00 38.97 16.7 8.4 10.8 803.8 12/16/2008 11:01 39.15 17 8.4 10.8 804.1 12/16/2008 11:02 38.97 17.2 8.4 10.8 816.9 12/16/2008 11:03 39.26 17.5 8.5 10.8 815 12/16/2008 11:04 39.83 17.4 8.5 10.8 820.3 12/16/2008 11:05 39.58 17.2 8.5 10.8 819.9 12/16/2008 11:06 39.69 17 8.5 10.8 812.5 12/16/2008 11:07 39.81 17.2 8.5 10.8 803.9 12/16/2008 11:08 39.89 17.4 8.5 10.9 808 12/16/2008 11:09 39.88 17.3 8.5 10.8 817 12/16/2008 11:10 39.39 17.5 8.5 10.8 822.3 12/16/2008 11:11 39.02 17.4 8.5 10.9 817.6 12/16/2008 11:12 39.41 17.5 8.5 10.9 810.6 12/16/2008 11:13 39.51 17.6 8.5 10.8 817 12/16/2008 11:14 39.26 17.5 8.5 10.9 813.8 12/16/2008 11:15 39.42 17.5 8.5 10.9 810.6 12/16/2008 11:16 39.24 17.8 8.5 10.9 808.5 12/16/2008 11:17 39.13 17.9 8.5 10.8 819.5 12/16/2008 11:18 39.7 17.8 8.6 10.9 816.3 12/16/2008 11:19 39.48 17.4 8.5 10.8 811.1 12/16/2008 11:20 39.74 17.3 8.6 10.8 811.2 12/16/2008 11:21 39.57 17.5 8.6 10.8 809.4 12/16/2008 11:22 39.61 17.7 8.6 10.9 801.4 12/16/2008 11:23 39.64 17.5 8.6 10.9 802.8 12/16/2008 11:24 39.54 17.6 8.6 10.9 794.3 12/16/2008 11:25 39.19 17.9 8.6 10.8 805.5 12/16/2008 11:26 39.27 17.7 8.6 10.8 810.3 12/16/2008 11:27 39.18 17.6 8.6 10.9 815.7 12/16/2008 11:28 39.29 17.6 8.6 10.9 805.1 12/16/2008 11:29 39.44 17.4 8.6 10.8 810.2 12/16/2008 11:30 39.09 16.8 8.6 10.8 812.3 12/16/2008 11:31 39.19 17.5 8.6 10.9 815.8 12/16/2008 11:32 39.24 17.4 8.6 10.9 817 12/16/2008 11:33 39.28 17.5 8.6 10.9 817.5 12/16/2008 11:34 39.42 17.7 8.6 10.9 816.3 12/16/2008 11:35 39.67 17.7 8.6 10.9 809.7

Page 11 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/16/2008 11:36 39.54 17.6 8.6 10.9 815.3 12/16/2008 11:37 39.55 17.7 8.6 10.9 811.5 12/16/2008 11:38 39.52 18.1 8.6 10.9 807.3 12/16/2008 11:39 39.67 18 8.6 10.9 815.8 12/16/2008 11:40 39.59 17.4 8.6 10.9 818.6 12/16/2008 11:41 39.36 17.5 8.6 10.9 821.5 12/16/2008 11:42 39.48 17.8 8.6 10.9 807.1 12/16/2008 11:43 39.15 17.8 8.6 10.9 820.8 12/16/2008 11:44 39.39 17.9 8.6 10.9 812.6 12/16/2008 11:45 39.12 17.9 8.7 10.9 818 12/16/2008 11:46 39.14 17.9 8.7 10.9 820.8 12/16/2008 11:47 39.54 17.8 8.7 10.9 812.4 12/16/2008 11:48 39.34 18.2 8.7 10.9 812.8 12/16/2008 11:49 39.67 17.8 8.7 10.9 815.6 12/16/2008 11:50 39.82 17.8 8.7 10.9 815.6 12/16/2008 11:51 39.5 17.9 8.7 10.9 812.1 12/16/2008 11:52 39.33 18 8.7 10.9 812.6 12/16/2008 11:53 39.25 18 8.7 10.9 814.7 12/16/2008 11:54 39.23 18.4 8.7 10.9 812.3 12/16/2008 11:55 39.17 18.5 8.7 10.9 815.6 12/16/2008 11:56 39.11 18.1 8.7 10.9 809.9 12/16/2008 11:57 39.39 18.2 8.7 10.9 821.5 12/16/2008 11:58 39.31 18.3 8.7 10.9 808.7 12/16/2008 11:59 39.51 18.1 8.7 10.9 818.1 12/16/2008 12:00 39.25 18 8.7 10.9 810.8 12/16/2008 12:01 39.32 18.1 8.7 10.9 809.1 12/16/2008 12:02 39.26 18.6 8.7 10.9 820.2 12/16/2008 12:03 39.14 18.2 8.7 10.9 820.6 12/16/2008 12:04 39.28 18.1 8.7 10.9 815.7 12/16/2008 12:05 39.25 18.1 8.7 10.9 811.4 12/16/2008 12:06 39.32 18.3 8.7 10.9 820 12/16/2008 12:07 39.19 18.2 8.7 10.9 821.4 12/16/2008 12:08 39.38 18.3 8.7 11 822.6 12/16/2008 12:09 39.21 18.3 8.7 10.9 824 12/16/2008 12:10 39.15 18 8.7 10.9 818.6 12/16/2008 12:11 38.94 17.9 8.7 10.9 816.4 12/16/2008 12:12 39.07 18.1 8.7 11 815.9 12/16/2008 12:13 39.03 18.5 8.7 11 824.5 12/16/2008 12:14 39.25 18.4 8.7 10.9 826.7 12/16/2008 12:15 39.47 17.9 8.7 10.9 820.7

Page 12 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/16/2008 12:16 39.19 17.9 8.7 10.9 814.6 12/16/2008 12:17 39.34 18 8.7 10.9 829.6 12/16/2008 12:18 39.13 17.8 8.7 10.9 816.6 12/16/2008 12:19 39.51 17.6 8.7 10.9 810.9 12/16/2008 12:20 39.3 17.2 8.7 10.9 811.8 12/16/2008 12:21 38.9 17.4 8.7 10.9 805.9 12/16/2008 12:22 39.24 17.7 8.7 10.9 806.3 12/16/2008 12:23 39.26 17.9 8.7 10.9 818.2 12/16/2008 12:24 39.68 18.1 8.7 10.9 812.2 12/16/2008 12:25 39.84 17.7 8.7 10.9 809.2 12/16/2008 12:26 33.7 12 4.9 10.9 814.6 12/16/2008 12:27 3.16 0.1 0.6 10.9 819.9 12/16/2008 12:28 20.92 11.2 7.5 11 812.1 12/16/2008 12:29 38.56 17.5 8.6 10.9 816.8 12/16/2008 12:30 39.05 17.8 8.6 10.9 818.9 12/16/2008 12:31 38.93 18.1 8.6 10.9 819.4 12/16/2008 12:32 38.94 18.1 8.6 10.9 820.1 12/16/2008 12:33 39.14 18.2 8.6 11 827.2 12/16/2008 12:34 39.46 18.5 8.6 11 824.5 12/16/2008 12:35 38.84 18.3 8.6 11 813.5 12/16/2008 12:36 39 18.5 8.6 11 815.7 12/16/2008 12:37 39.11 18.3 8.6 11 808.6 12/16/2008 12:38 38.62 18.3 8.6 11 825.2 12/16/2008 12:39 38.94 18.7 8.6 11 821.6 12/16/2008 12:40 38.6 18.3 8.6 10.9 818.2 12/16/2008 12:41 38.88 18.2 8.6 11 815 12/16/2008 12:42 38.8 18.1 8.6 11 819.2 12/16/2008 12:43 38.72 18.5 8.6 11 814.5 12/16/2008 12:44 38.63 18.5 8.6 11 813.3 12/16/2008 12:45 38.62 18.5 8.7 11 814.8 12/16/2008 12:46 39.04 18.4 8.6 11 811.8 12/16/2008 12:47 38.73 18.2 8.6 10.9 809.1 12/16/2008 12:48 39.01 18.1 8.6 11 809.4 12/16/2008 12:49 39.08 18.2 8.6 10.9 820.8 12/16/2008 12:50 39.38 17.7 8.7 10.9 814.9 12/16/2008 12:51 39.51 17.9 8.7 11 815.5 12/16/2008 12:52 39.24 18.1 8.6 11 820.6 12/16/2008 12:53 39.11 18.2 8.7 11 821.9 12/16/2008 12:54 39.52 18.6 8.7 11 820 12/16/2008 12:55 39.46 18.6 8.7 11 814.6

Page 13 of 14

## SO2 & NOx CEM Data

Date Time SO21 NOX1 CO21 OXY1 FLO1 12/16/2008 12:56 39.17 18.4 8.7 10.9 801.9 12/16/2008 12:57 39.38 18.5 8.7 10.9 806.5 12/16/2008 12:58 39.27 18.6 8.7 11 818.4 12/16/2008 12:59 38.97 18.8 8.7 11 817.5 12/16/2008 13:00 39.08 18.4 8.7 10.9 826.8 12/16/2008 13:01 39.28 18.2 8.7 11 819.2 12/16/2008 13:02 38.88 18.4 8.7 11 811.1 12/16/2008 13:03 39.03 18.9 8.7 11 823.4 12/16/2008 13:04 38.98 18.8 8.7 11 821.7 12/16/2008 13:05 38.93 18.4 8.7 11 813.1 12/16/2008 13:06 39.13 18.3 8.7 11 811.5 12/16/2008 13:07 38.75 18.6 8.7 11 813.1 12/16/2008 13:08 39.07 18.8 8.7 11 812.9 12/16/2008 13:09 39.47 18.7 8.7 11 816.7 12/16/2008 13:10 39.24 18.3 8.7 11 819.6 12/16/2008 13:11 38.92 18.4 8.7 11 818.3 12/16/2008 13:12 39.1 18.4 8.7 11 816.4 12/16/2008 13:13 39.48 18.7 8.7 11 812.1 12/16/2008 13:14 39.28 18.9 8.7 11 818.7 12/16/2008 13:15 39.15 18.3 8.7 11 813.1 12/16/2008 13:16 39.23 18.4 8.7 11 823.5 12/16/2008 13:17 39.21 18.5 8.7 11 812 12/16/2008 13:18 39.47 18.6 8.7 11 819.5 12/16/2008 13:19 39.21 19 8.7 10.9 824.3 12/16/2008 13:20 39.13 18.3 8.7 11 807.8 A verages 39.435 17.78 8.512 10.86 813.25

Page 14 of 14

## APPENDIX G

VISIBLE EMISSIONS DATA SHEET

## APPENDIX H

TEST PARTICIPANTS

## TEST PARTICIPANTS

AIR SERVICES GROUP TEST TEAM

Jorge Varino Environmental Technician – Team Lead Gary Barber Environmental Technician

Scott Given Environmental Technician Ryan Newell Associate Technician David A. Smith Coordinator, Air Services Group

PROCESS DATA

Raymond A. McDarby Senior Environmental Technician

FUEL ANALYSIS

John McDaniel Senior Engineer ing Fellow– Polk Power Station

REPORT PREPARATION

Raymond A. McDarby Senior Environmental Technician
QUALITY ASSURANCE / QUALITY CONTROL

Raymond A. McDarby Senior Environmental Technician

POLK POWER STATION

Michael Perkins Environmental Coordinator Joshua Ellwein Principal Engineer