### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Saturday, January 22, 2011 Page 1 of 11

### Facility Information:

Central Power and Lime, Inc.

10311 Cement Plant Road

Brooksville FL 34605
Contact: Larry Roberts
Phone: 352-799-7881
Fax:
Email: Lroberts@deltapowerservices.com Testing Company: Koogler and Associates, Inc.

4014 NW 13th St

Gainesville FL 32609
Contact: Dr. Max Lee
Phone: 352-377-5822
Fax:
Email: mlee@kooglerassociates.com

Air Permit Number:
0530021-011-AV Permitted Source ID/Name:
Boiler 1
Permitted Maximum Process Rate:
150 MW Max. Normal Operation Process Rate:
150 MW Target Process Test Rate
135 MW

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: Power Plant Boiler with Dry Limestone Injection Scrubbing follwed with a Baghouse System. The emissions unit is a net delivered 150MW fossil fuel fired boiler with a 320 foot stack. The primary fuel burned is coal, with new distillate No. 2 fuel oil used for startup. Control activity includes dru limestone injection scrubbing followed with a fabric filter baghouse system. The exit diameter is 16 feet and exit temperature is 300 degrees F. The volumetric flow rate is 840,000 acfm. Industry/SCC/NAIS

Sampling Location Information:

Test Parameter Information: AFS #: FRS #:

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Pulverized Coal: Dry Bottom (Bituminous Coal)

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
Power Plant Duct 0 0 0 1 0 1 144 144

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 120 0 Power Plant Duct Total organic compounds

(TOC) as Methane Method 25A 3 120 0 Only For the Method 25A -CH4 Runs Power Plant Duct



### Saturday, January 22, 2011 Page 2 of 11

### The following describes any modifications and/or deviations to the applicable test

methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates.

Total organic compounds (TOC) as Propane Method 25A 3 120 0 For Method 25A runs 1-3 Power Plant Duct O2 Method 3A O2 3 120 0 Power Plant Duct



### Saturday, January 22, 2011 Page 3 of 11

### Sampling / Stack Data Results Summary



### Location Power Plant Duct - Method 10 Average
Run Number

Test Date 14 13.9 13.9
Run Start Time
Run Finish Time 7.1 7.2 7.3 Carbon Dioxide, % 1500 1500 1500 1,500.000 Oxygen, % 10 0 0 3.333 Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Power Plant Duct Power Plant Duct Power Plant

Duct Moisture, % 48 48 48 48.000 Fuel Type

Fw Method 10 Method 10 Method 10

Fc 1 2 3 2.000



### Location Power Plant Duct - Method 25A Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Saturday, January 22, 2011 Page 4 of 11

### Location Power Plant Duct - Method 25A 3 Average

Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw
Fc



### Location Power Plant Duct - Method 3A O2 Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw
Fc



### Saturday, January 22, 2011 Page 5 of 11

### Emissions Summary

Process Run Data 

### Location: Power Plant Duct - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 5.20E-01 5.90E-01 5.16E-01 0.542
ppm 4.83E+02 5.44E+02 4.72E+02 499.667 ppm@7%O2 4.87E+02 5.52E+02 4.82E+02 507.000



### Location: Power Plant Duct - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 -6.02E-06 6.37E-06 -2.16E-04 0.000
ppm -9.90E-03 1.04E-02 -3.53E-01 -0.118 ppm@7%O2 -9.83E-03 1.04E-02 -3.53E-01 -0.117


### Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 -1.65E-05 1.75E-05 -5.94E-04 0.000
ppm -9.90E-03 1.04E-02 -3.53E-01 -0.118 ppm@7%O2 -9.83E-03 1.04E-02 -3.53E-01 -0.117



### Location: Power Plant Duct - Method 25A 3 

### Compound: Total organic compounds (TOC) as Average Run CH4-1 CH4-2 CH4-3 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000
ppm 0.00E+00 0.00E+00 0.00E+00 0.000 ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000


### Compound: Total organic compounds (TOC) as Average Run CH4-1 CH4-2 CH4-3 lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000
ppm 0.00E+00 0.00E+00 0.00E+00 0.000 ppm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000



### Saturday, January 22, 2011 Page 6 of 11

### Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value
1 Generator Rate 136.4 MW 135



### 1 Heat Input 1409 Million Btus/hr 1400

1 Coal Feed Rate 55.1 TPH 55

2 Generator Rate 135.4 MW 135



### 2 Heat Input 1419 Million Btus/hr 1400

2 Coal Feed Rate 55.5 TPH 55

3 Generator Rate 136.1 MW 135



### 3 Heat Input 1423 Million Btus/hr 1400

3 Coal Feed Rate 55.7 TPH 55



### Run Name Value UOM Comments Target Value
1 DRY LIMESTONE INJECTION 20.92 0



### 2 DRY LIMESTONE INJECTION 20.92 0

3 DRY LIMESTONE INJECTION 20.92 0



### 1 BAGHOUSE 0 0

2 BAGHOUSE 0 0

3 BAGHOUSE 0 0



### Saturday, January 22, 2011 Page 7 of 11

### Sampling / Stack Data Results Detail



### Location Power Plant Duct - Method 10 Average Run Number Test Date 14 13.9 13.9 Run Start Time Run Finish Time 7.1 7.2 7.3 Carbon Dioxide, % 1500 1500 1500 1,500.000 Oxygen, % 10 0 0 3.333 Fuel Factor 8/31/2010 8/31/2010 8/31/2010 Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Power Plant Duct Power Plant

Duct Power Plant

Duct Moisture, % 48 48 48 48.000 Analyzer Make 1 1 1 1.000 Analyzer Model Nitrogen Nitrogen Nitrogen Analyzer Serial Number 1.36 0 0 0.453 Operating Range -99.81 -99.92 -99.92 -99.883 Operating Units 0 0 0 No. Readings/Avg. CO Mid CO Mid CO Mid Calibration Set -0.5 -1.4 -1.59 -1.163 Calibration Pre Zero Cylinder ID 0 0 0 Calibration Pre Zero Cylinder Instrument Response Nitrogen Nitrogen Nitrogen Calibration Pre Zero Cylinder Bias 0 0 0 0.000 Calibration Pre Zero Cylinder Drift -99.92 -99.92 -99.92 -99.920 Calibration Pre High Cylinder ID 0.1099999999 99999 0 0

Calibration Pre High Cylinder Instrument Response CO Mid CO Mid CO Mid Calibration Pre High Cylinder Bias 426.6 424.3 425.2 425.367 Calibration Pre High Cylinder Drift -1.4 -1.59 -1.52 -1.503 Calibration Post Zero Cylinder ID 0.9 0.19 7.000000000 00001E-02 Calibration Post Zero Cylinder Instrument Response 464.7 515 446.4 475.367 Calibration Post Zero Cylinder Bias ppmvd ppmvd ppmvd Calibration Post Zero Cylinder Drift 483.2556 543.749 472.0962 499.700 Calibration Post High Cylinder ID ppmvd ppmvd ppmvd Calibration Post High Cylinder Instrument Response Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Calibration Post High Cylinder Bias 9780 9780 9780 9,780.000 Calibration Post High Cylinder Drift 10640 10640 10640 10,640.000 Cavg 1800 1800 1800 1,800.000 Cavg Units 0.99 1 0.98 Cgas 0 0 0 0.000 Cgas Units Fuel Type Fw Method 10 Method 10 Method 10 Fc 1 2 3 2.000 Cgasw 3:00:00 PM 5:25:00 PM 7:48:00 PM Cgasw Units 5:00:00 PM 7:25:00 PM 9:48:00 PM



### Saturday, January 22, 2011 Page 8 of 11

### Location Power Plant Duct - Method 25A Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Saturday, January 22, 2011 Page 9 of 11

### Location Power Plant Duct - Method 25A 3 Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Saturday, January 22, 2011 Page 10 of 11

### Location Power Plant Duct - Method 3A O2 Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Saturday, January 22, 2011 Page 11 of 11