### Name: Robert A. Greco

Title: Manager Air Quality Company: We Energies Sign Date: 6/30/2010 Name: Scott W. Banach Title: Director, Project Engineering Company:Platt Environmental Services, Inc. Sign Date: 6/30/2010 Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Monday, February 07, 2011 Page 1 of 14

### 6/30/2010

Facility Information: Valley (ORIS Facility ID #4042) 1035 West Canal Street

Milwaukee WI53233 Contact:Robert A. Greco Phone:(414) 221-5441 Fax: (414) 221-2022 Email: bob.greco@we-energies.com Testing Company: Platt Environmental Services, Inc. 1520 Kensington Road, Suite 204

Oak Brook IL60523 Contact:Scott W. Banach Phone:(630) 521-9400 Fax: (630) 521-9494 Email:sbanach@plattenv.com

Air Permit Number: 4042 Permitted Source ID/Name: Valley 4 Permitted Maximum Process Rate: N/A Max. Normal Operation Process Rate: N/A Target Process Test Rate N/A

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: The Valley Power Plant Boilers 1, 2, 3, and 4 are Riley Stoker, dry bottom, wall-fired, pulverized coal-fired boilers which currently fire western bituminous coals. These units are also permitted to fire natural gas and propane for unit startup, flame stabilization, and supplemental firing. In 1994, low Nox burners were installed on all four boilers, and the original electrostatic precipitators on all four boilers were replaced with high efficiency fabric filter baghouses. Industry/SCC/NAIS221112

Sampling Location Information:

Test Parameter Information: AFS #:5507900191 FRS #:20847

SCC / Description10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Pulverized Coal: Dry Bottom (Bituminous Coal)

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width Stack exit 0 107 474 4 130.3 24 152 114

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location % H2O Method 1 - 4 3 180 0 Stack Exit Carbon Monoxide Method 10 3 120 0 Stack Exit Formaldehyde Method 0011 3 120 0 Stack Exit 2,3,7,8-TCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0 Stack Exit 

### Monday, February 07, 2011 Page 2 of 14

### 6/30/2010 1,2,3,7,8,9-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0 Stack Exit OCDD Method 23 3 480 0 Stack Exit 2,3,7,8-TCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0 Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 Stack Exit OCDF Method 23 3 480 0 Stack Exit Other TCDD Method 23 0 Stack Exit Other PeCDD Method 23 0 Stack Exit Other HxCDD Method 23 0 Stack Exit Other HpCDD Method 23 0 Stack Exit Other TCDF Method 23 0 Stack Exit Other PeCDF Method 23 0 Stack Exit Other HxCDF Method 23 0 Stack Exit Other HpCDF Method 23 0 Stack Exit Total Dioxins Method 23 3 480 0 Stack Exit Total Furans Method 23 3 480 0 Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0 Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 Stack Exit 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 Stack Exit
2,3',4,4',5,5'-HxCB (PCB167)Method 23 3 480 0 Stack Exit 3,3',4,4',5,5'-HxCB (PCB169)Method 23 3 480 0 Stack Exit 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 Stack Exit
Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Exit
Hydrogen Fluoride Method 26A 3 180 0 Stack Exit Hydrogen Chloride Method 26A 3 180 0 Stack Exit Hydrogen Fluoride Method 26 3 180 0 Stack Exit Hydrogen Chloride Method 26 3 180 0 Stack Exit Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Organic Condensible

Particulate OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit



### Monday, February 07, 2011 Page 3 of 14

### 6/30/2010

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. All methods described in the EU MACT ICR were used.

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Beryllium Method 29 3 240 0 Stack Exit Cobalt Method 29 3 240 0 Stack Exit Nickel Method 29 3 240 0 Stack Exit Antimony Method 29 3 240 0 Stack Exit Arsenic Method 29 3 240 0 Stack Exit Selenium Method 29 3 240 0 Stack Exit Lead Method 29 3 240 0 Stack Exit Filterable Particulate Method 29 3 240 0 Stack Exit Chromium Method 29 3 240 0 Stack Exit Manganese Method 29 3 240 0 Stack Exit Cadmium Method 29 3 240 0 Stack Exit O2 Method 3A O2 3 240 0 Stack Exit O2 Method 3A O2 3 120 0 Stack Exit Co2 Method 3A CO2 3 120 0 Stack Exit Co2 Method 3A CO2 3 240 0 Stack Exit O2 Method 3A O2 3 480 0 Stack Exit Co2 Method 3A CO2 3 480 0 Stack Exit Total Particulate Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Inorganic (Aqueous)

Condensible Part. Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Organic Condensible

Particulate Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Filterable Particulate Method 5 3 240 0 Stack Exit Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet stacks. Delete OTM27/OTM28 test. Stack Exit

Sulfur Dioxide Method 6C 3 180 0 Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0 Stack Exit



### Monday, February 07, 2011 Page 4 of 14

### 6/30/2010

Sampling / Stack Data Results Summary


### LocationStack Exit - Method 29 Average Run Number M29-1 M29-2 M29-3 Test Date 4/27/2010 4/29/2010 4/30/2010 Run Start Time 8:05:00 AM 7:40:00 AM 7:40:00 AM

Run Finish Time 12:17:00 PM 11:50:00 AM11:54:00 AM

Net Run Time, minutes 240 240 240 Dry Gas Meter Volume Sampled, dscf 143.619 142.108 144.265 143.331 Moisture Content of Stack Gas, % 6.61 7.42 7.83 7.287 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 12.3 12.4 12.6 12.433 Oxygen, % 6.2 6 6 6.067 Average Stack Gas Temperature, °F 313.67 315.63 315.46 314.920 Dry Volumetric Flow Rate, dry scfm 167,704.0 166,810.8 168,010.9167,508.567 Actual Wet Volumetric Flue Gas Flow Rate, acfm 280,568.4 282,229.0 285,766.8282,854.733 Percent Isokinetic of Sampling Rate, % 103.3 102.8 103.6 103.233 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000



### Monday, February 07, 2011 Page 5 of 14

### 6/30/2010

LocationStack Exit - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2 Fw Fc



### Monday, February 07, 2011 Page 6 of 14

### 6/30/2010

Emissions Summary


### Location: Stack Exit - Method 29 Compound: Antimony Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.0028 0.0028 0.0028 0.003 Elb/hr 4.32E-04 4.35E-04 4.31E-04 0.000 lb/mmBtuO2 5.98E-07 5.96E-07 5.87E-07 0.000 mg/dscm 6.89E-04 6.96E-04 6.86E-04 0.001 mg/dscm@7%O2 6.52E-04 6.49E-04 6.40E-04 0.001 

### Compound: Arsenic Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.0028 0.0028 0.0028 0.003 Elb/hr 4.32E-04 4.35E-04 4.31E-04 0.000 lb/mmBtuO2 5.98E-07 5.96E-07 5.87E-07 0.000 mg/dscm 6.89E-04 6.96E-04 6.86E-04 0.001 mg/dscm@7%O2 6.52E-04 6.49E-04 6.40E-04 0.001 

### Compound: Beryllium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.0007 0.0007 0.0007 0.001 Elb/hr 1.08E-04 1.09E-04 1.08E-04 0.000 lb/mmBtuO2 1.49E-07 1.49E-07 1.47E-07 0.000 mg/dscm 1.72E-04 1.74E-04 1.71E-04 0.000 mg/dscm@7%O2 1.63E-04 1.62E-04 1.60E-04 0.000 

### Compound: Cadmium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.0007 0.0007 0.0007 0.001 Elb/hr 1.08E-04 1.09E-04 1.08E-04 0.000 lb/mmBtuO2 1.49E-07 1.49E-07 1.47E-07 0.000 mg/dscm 1.72E-04 1.74E-04 1.71E-04 0.000 mg/dscm@7%O2 1.63E-04 1.62E-04 1.60E-04 0.000 

### Compound: Chromium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 1.43631 0.91969 0.33116 0.896 Elb/hr 2.22E-01 1.43E-01 5.10E-02 0.139 lb/mmBtuO2 3.07E-04 1.96E-04 6.94E-05 0.000 mg/dscm 3.53E-01 2.29E-01 8.11E-02 0.221 mg/dscm@7%O2 3.34E-01 2.14E-01 7.57E-02 0.208 

### Compound: Cobalt Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.02302 0.01211 0.00709 0.014 Elb/hr 3.56E-03 1.88E-03 1.09E-03 0.002



### Monday, February 07, 2011 Page 7 of 14

### 6/30/2010 lb/mmBtuO2 4.91E-06 2.58E-06 1.49E-06 0.000 mg/dscm 5.66E-03 3.01E-03 1.74E-03 0.003 mg/dscm@7%O2 5.35E-03 2.81E-03 1.62E-03 0.003 

### Compound: Filterable Particulate Average RunNumber M29-1 M29-2 M29-3 Mass_mg 10.7 14.4 21.8 15.633 Elb/hr 1.65E+00 2.24E+00 3.36E+00 2.417 lb/mmBtuO2 2.28E-03 3.06E-03 4.57E-03 0.003 mg/dscm 2.63E+00 3.58E+00 5.34E+00 3.850 mg/dscm@7%O2 2.49E+00 3.34E+00 4.98E+00 3.603 

### Compound: Lead Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.00286 0.00167 0.00153 0.002 Elb/hr 4.42E-04 2.59E-04 2.36E-04 0.000 lb/mmBtuO2 6.10E-07 3.55E-07 3.21E-07 0.000 mg/dscm 7.03E-04 4.15E-04 3.75E-04 0.000 mg/dscm@7%O2 6.65E-04 3.87E-04 3.50E-04 0.000 

### Compound: Manganese Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.2089 0.0974 0.0506 0.119 Elb/hr 3.23E-02 1.51E-02 7.79E-03 0.018 lb/mmBtuO2 4.46E-05 2.07E-05 1.06E-05 0.000 mg/dscm 5.14E-02 2.42E-02 1.24E-02 0.029 mg/dscm@7%O2 4.86E-02 2.26E-02 1.16E-02 0.028 

### Compound: Nickel Average RunNumber M29-1 M29-2 M29-3 Mass_mg 2.03005 0.66915 0.45425 1.051 Elb/hr 3.14E-01 1.04E-01 7.00E-02 0.163 lb/mmBtuO2 4.33E-04 1.42E-04 9.52E-05 0.000 mg/dscm 4.99E-01 1.66E-01 1.11E-01 0.259 mg/dscm@7%O2 4.72E-01 1.55E-01 1.04E-01 0.244 

### Compound: Selenium Average RunNumber M29-1 M29-2 M29-3 Mass_mg 0.018 0.0077 0.0075 0.011 Elb/hr 2.78E-03 1.20E-03 1.16E-03 0.002 lb/mmBtuO2 3.84E-06 1.64E-06 1.57E-06 0.000 mg/dscm 4.43E-03 1.91E-03 1.84E-03 0.003 mg/dscm@7%O2 4.19E-03 1.78E-03 1.72E-03 0.003



### Location: Stack Exit - OTM - 27/28 Compound: Filterable Particulate Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2MOTM27/OTM28-3



### Monday, February 07, 2011 Page 8 of 14

### 6/30/2010

Process Run Data Mass_mg 6.9 6.4 5.8 6.367 lb/mmBtuO2 1.68E-03 1.49E-03 1.32E-03 0.001 

### Compound: Filterable PM2.5 Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2MOTM27/OTM28-3 Mass_mg 5.3 4.9 5.2 5.133 lb/mmBtuO2 1.29E-03 1.14E-03 1.18E-03 0.001 

### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2MOTM27/OTM28-3 Mass_mg 25 9.9 27.2 20.700 lb/mmBtuO2 6.10E-03 2.31E-03 6.17E-03 0.005 

### Compound: Organic Condensible Particulate Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2MOTM27/OTM28-3 Mass_mg 1.1 6.8 4.5 4.133 lb/mmBtuO2 2.68E-04 1.59E-03 1.02E-03 0.001 

### Compound: Total Particulate Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2MOTM27/OTM28-3 Mass_mg 33 23.1 37.5 31.200 lb/mmBtuO2 8.05E-03 5.39E-03 8.50E-03 0.007 

### Compound: Total PM2.5 Average RunNumber MOTM27/OTM28-1 MOTM27/OTM28-2MOTM27/OTM28-3 Mass_mg 31.4 21.6 36.9 29.967 lb/mmBtuO2 7.66E-03 5.04E-03 8.37E-03 0.007



### Monday, February 07, 2011 Page 9 of 14

### 6/30/2010

Process Run Data



### Run Name Value UOM Comments Target Value 1 Bituminous Coal Burned 0.03421000 Tons/hr 0 

### 2 Bituminous Coal Burned 0.0361000 Tons/hr 0 3 Bituminous Coal Burned 0.03681000 Tons/hr 0 1 Average Heat Input 756.8 MMBtu/hr 0 

### 2 Average Heat Input 776.1 MMBtu/hr 0 3 Average Heat Input 806.9 MMBtu/hr 0 1 Steam Output 587.51000 lb steam/hr 0 

### 2 Steam Output 599.171000 lb steam/hr 0 3 Steam Output 620.171000 lb steam/hr 0 1 Synfuel Firing Rate 0 1000 Tons/hr 0 

### 2 Synfuel Firing Rate 0 1000 Tons/hr 0 3 Synfuel Firing Rate 0 1000 Tons/hr 0 1 Petroleum Coke Firing Rate 0 1000 Tons/hr 0 

### 2 Petroleum Coke Firing Rate 0 1000 Tons/hr 0 3 Petroleum Coke Firing Rate 0 1000 Tons/hr 0 1 Coal Gas Firing Rate 0 Ft^3/min 0 

### 2 Coal Gas Firing Rate 0 Ft^3/min 0 3 Coal Gas Firing Rate 0 Ft^3/min 0 1 Fuel Oil Firing Rate 0 gal/hr 0 

### 2 Fuel Oil Firing Rate 0 gal/hr 0 3 Fuel Oil Firing Rate 0 gal/hr 0 1 Flue Gas Flow Rate 0 0 

### 1 Pressure Drop Across FGD (if applicable) 0 in H20 0 1 FGD Scrubber Liquor pH 0 pH 0 

### 1 FGD Scrubber Liquor Flow Rate 0 gal/min 0 1 Sorbent Type and Sorbent Injection Rate (if applicable) 0 lb/hr 0

1 Flue Gas Oxygen Content 6.2 % 0 

### 1 Flue Gas Carbon Dioxide Content 12.3 % 0 1 Flue Gas Moisture Content 7.1 % 0 1 Flue Gas Sampling Point Temperature 312.8 Deg F 0 

### 1 Flue Gas Pressure 0.936 atm 0 1 Standard Pressure 1 atm 0 1 Standard Temperature 63.33 Deg F 0



### Monday, February 07, 2011 Page 10 of 14

### 6/30/2010

APCD Run Data

Process Lab Run Data 1 Unit Gross Electrical Output 85.83 Mwe 0 

### 1 Unit Net Electric Generation 78.76 MWh 0

Run Name Value UOM Comments Target Value 1 BAGHOUSE 2.68 in H2O 0.25 2 BAGHOUSE 2.8 in H2O 0.25 

### 3 BAGHOUSE 3.48 in H2O 0.25

Run Name ValueUOM Comments 1 Fuel Higher Heating Value 13108Btu/lb 

### 1 Fuel Moisture 5.03 % 1 Fuel Mercury Content 0.012 ppm 1 Fuel Cadmium Content 0.11 ppm 1 Ultimate/Proximate Analysis 0 

### 1 Fuel Nickel Content 3 ppm 1 Fuel Arsenic Content 0.55 ppm 1 Fuel Chromium Content 3.7 ppm 

### 1 Fuel Beryllium Content 0.57 ppm 1 Fuel Lead Content 5.2 ppm 1 Fuel Manganese Content 9.6 ppm 1 Fuel Chlorine Content 420 ppm 

### 1 Fuel Fluorine Content 84 ppm 2 Fuel Higher Heating Value 12919Btu/lb 2 Fuel Moisture 4.5 % 

### 2 Fuel Mercury Content 0.025 ppm 2 Fuel Cadmium Content 0.12 ppm 2 Ultimate/Proximate Analysis 0 2 Fuel Nickel Content 3.4 ppm 

### 2 Fuel Arsenic Content 0.53 ppm 2 Fuel Chromium Content 3.3 ppm 2 Fuel Beryllium Content 0.62 ppm 

### 2 Fuel Lead Content 5.3 ppm 2 Fuel Manganese Content 10 ppm 2 Fuel Chlorine Content 360 ppm 2 Fuel Fluorine Content 91 ppm 

### 3 Fuel Higher Heating Value 12815Btu/lb 3 Fuel Moisture 5.78 % 3 Fuel Mercury Content 0.014 ppm 3 Fuel Cadmium Content 0.12 ppm 

### Monday, February 07, 2011 Page 11 of 14

### 6/30/2010

3 Ultimate/Proximate Analysis 0 

### 3 Fuel Nickel Content 3.7 ppm 3 Fuel Arsenic Content 0.7 ppm 3 Fuel Chromium Content 3.2 ppm 3 Fuel Beryllium Content 0.6 ppm 

### 3 Fuel Lead Content 5.9 ppm 3 Fuel Manganese Content 13 ppm 3 Fuel Chlorine Content 280 ppm 

### 3 Fuel Fluorine Content 89 ppm

Monday, February 07, 2011 Page 12 of 14

### 6/30/2010

Sampling / Stack Data Results Detail


### LocationStack Exit - Method 29 Average Run Number M29-1 M29-2 M29-3 Test Date 4/27/2010 4/29/2010 4/30/2010 Run Start Time 8:05:00 AM7:40:00 AM7:40:00 AM Run Finish Time 12:17:00 PM11:50:00 AM11:54:00 AM Net Traversing Points 48 48 48 Net Run Time, minutes 240 240 240 Nozzle Diameter, inches 0.276 0.276 0.276 0.276 Pitot Tube Coefficient 0.84 0.84 0.84 0.840 Dry Gas Meter Calibration Factor 0.993 0.993 0.993 0.993 Barometric Pressure, inches of Mercury 29.2 29.2 29.2 29.200 Average Orifice Meter Differential, inches H2O 1.12 1.10 1.13 1.117 Dry Gas Meter Volume Sampled, cubic feet 153.060 152.011 154.857 153.309 Average Dry Gas Meter Temperature, °F 86.86 88.86 90.82 88.847 Dry Gas Meter Volume Sampled, dscf 143.619 142.108 144.265 143.331 Total Moisture Liquid collected, g 215.8 242 260.4 239.400 Volume of Water Vapor, standard cubic feet 10.16 11.39 12.26 11.270 Moisture Content of Stack Gas, % 6.61 7.42 7.83 7.287 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9339 0.9258 0.9217 0.927 Carbon Dioxide, % 12.3 12.4 12.6 12.433 Oxygen, % 6.2 6 6 6.067 Carbon Monoxide & Nitrogen, % 81.5 81.6 81.4 81.500 Fuel Factor 1.20 1.20 1.18 Dry Molecular Weight, lb/lb-Mole 30.22 30.22 30.26 30.233 Wet Molecular weight, lb/lb-Mole 29.41 29.31 29.30 29.340 Flue Gas Static Pressure, inches of H2O -15.5 -15.5 -15.9 -15.633 Absolute Flue Gas Pressure, inches of Mercury 28.06 28.06 28.03 28.050 Average Stack Gas Temperature, °F 313.67 315.63 315.46 314.920 Average Velocity Head, inches of H2O 0.3122879413 220660.314141373

7971190.321655491

693944 0.316
Average Stack Gas Velocity, feet/second 38.86 39.09 39.58 39.177 Stack Cross-Sectional Area, square feet 120.333 120.333 120.333 120.333 Dry Volumetric Flow Rate, dry scfm 167,704.0 166,810.8 168,010.9167,508.567 Actual Wet Volumetric Flue Gas Flow Rate, acfm 280,568.4 282,229.0 285,766.8282,854.733 Percent Isokinetic of Sampling Rate, % 103.3 102.8 103.6 103.233 Percent Excess Air, % 40.5 38.6 38.7 39.267 F-Factor, dscfm/MMBtu @ %O2 9780 9780 97809,780.000 Round Duct Diameter, inches 0 0 0 Rectangular Duct Width, inches 152 152 152 Rectangular Duct Length, inches 114 114 114 Fw 10640 10640 1064010,640.000 Fc 1800 1800 18001,800.000



### Monday, February 07, 2011 Page 13 of 14

### 6/30/2010

LocationStack Exit - OTM - 27/28 Average Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Monday, February 07, 2011 Page 14 of 14