Name: Louis A. Florence Jr.

Title: President

Company: TransAlta Centralia Generation LLC

Sign Date: 9/3/2010

Name: Kevin Donahoe

Title: Project Manager

Company: The Avogadro Group Inc.

Sign Date: 8/30/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, February 28, 2011 Page 1 of 25
9/3/2010

Facility Information:

TransAlta Centralia Generation LLC

913 Big Hanaford Road

Centralia W 98531

Contact: Timothy Weber

Phone: 360-330-2346

Fax: 360-330-2367

Email: Tim_Weber@transalta.com

Testing Company:

The Avogadro Group Inc.

303 SW 153rd Drive, Suite 215

Beaverton OR 97006

Contact: Kevin Donahoe

Phone: 503-658-2091

Fax: 503-427-1153

Email: kdonahoe@avogadrogroup.com

Air Permit Number:

003845

Permitted Source ID/Name:

BW21 TransAlta Centralia Generation Unit 1

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Tangentally fired, dry bottom boiler, using Overfire Air for NOx control. Flue Gas travels through two sets of 

electrostatic precipitators before being discharged to a bypass stack (startups and emergency) or to a wet Flue Gas 

Desulfurization System and out the FGDS stack (normal operation).

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 5304110010 FRS #: 003845

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 357 0 0 357 2736 900 4 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Monday, February 28, 2011 Page 2 of 25
9/3/2010

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Stack Exit Total PCBs Method 23 3 480 0

Stack Exit Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Monday, February 28, 2011 Page 3 of 25
9/3/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

In this section, identify the promulgation date of any specified test method that you use for determining the 

procedures followed. This field is also used to document any modifications that are necessary to conduct the 

emissions test if they are outside the requirements of the cited method. If this modification was approved verbally by 

a regulatory agency, the name and date of approval should be included. Written formal approval should be attached 

to this file using the "Attach File" button. Test procedures that are different from those published in the Federal 

Register should be attached using the "Attach File" button.

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Magnesium Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Mercury Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Co2 Method 3A CO2 3 240 0

Stack Exit Co2 Method 3A CO2 3 120 0

Stack Exit O2 Method 3A O2 3 240 0

Stack Exit O2 Method 3A O2 3 120 0

Stack Exit O2 Method 3A O2 3 480 0

Stack Exit Co2 Method 3A CO2 3 480 0

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Filterable Particulate Method 5 3 240 0

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Monday, February 28, 2011 Page 4 of 25
9/3/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 1 - 4

Average

Run Number 1 2 3

Test Date 3/24/2010 3/25/2010 3/25/2010

Run Start Time 11:53:00 AM 7:20:00 

AM

2:17:00 PM

Run Finish Time 4:19:00 PM 11:51:00 

AM

6:28:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 150.106 149.359 156.261 151.909

Moisture Content of Stack Gas, % 15.53 17.91 17.89 17.110

Moisture Saturation at Stack Gas Temperature, % 16.27 16.26 16.32 16.283

Carbon Dioxide, % 14.098 13.798 13.929 13.942

Oxygen, % 5.392 5.733 5.612 5.579

Average Stack Gas Temperature, °F 132.33 132.08 132.25 132.220

Dry Volumetric Flow Rate, dry scfm 1,758,002.3 1,746,046.4 1,693,253.7 1,732,434.13

3

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,364,818.7 2,381,918.8 2,311,433.0 2,352,723.50

0

Percent Isokinetic of Sampling Rate, % 98.1 98.3 106.0 100.800

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 28, 2011 Page 5 of 25
9/3/2010

Location Stack Exit - Method 23

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 28, 2011 Page 6 of 25
9/3/2010

Location Stack Exit - Method 29 

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Monday, February 28, 2011 Page 7 of 25
9/3/2010

Emissions Summary

Location: Stack Exit - Method 1 - 4

Compound: % H2O

Average

RunNumber 1 2 3

Mass_mg #Num!

Percent(%) 0.000

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000105 0.0000000145 0.00000000876 0.000

lb/mmBtuO2 8.23E-13 1.56E-12 9.17E-13 0.000

ng/dscm 9.82E-04 1.85E-03 1.09E-03 0.001

ng/dscm@7%O2 8.96E-04 1.70E-03 9.96E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000745 0.00000000823 0.00000000632 0.000

lb/mmBtuO2 5.84E-13 8.85E-13 6.62E-13 0.000

ng/dscm 6.97E-04 1.05E-03 7.89E-04 0.001

ng/dscm@7%O2 6.36E-04 9.63E-04 7.21E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000899 0.00000000993 0.00000000762 0.000

lb/mmBtuO2 7.04E-13 1.07E-12 7.98E-13 0.000

ng/dscm 8.41E-04 1.27E-03 9.51E-04 0.001

ng/dscm@7%O2 7.67E-04 1.17E-03 8.69E-04 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000125 0.0000000144 0.0000000166 0.000

lb/mmBtuO2 9.79E-13 1.55E-12 1.74E-12 0.000

ng/dscm 1.17E-03 1.84E-03 2.07E-03 0.002

ng/dscm@7%O2 1.07E-03 1.69E-03 1.89E-03 0.002

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000064 0.00000000487 0.00000000448 0.000

lb/mmBtuO2 5.01E-13 5.24E-13 4.69E-13 0.000

ng/dscm 5.99E-04 6.22E-04 5.59E-04 0.001

ng/dscm@7%O2 5.47E-04 5.71E-04 5.11E-04 0.001

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Monday, February 28, 2011 Page 8 of 25
9/3/2010

Mass_mg 0.0000000117 0.0000000134 0.0000000155 0.000

lb/mmBtuO2 9.17E-13 1.44E-12 1.62E-12 0.000

ng/dscm 1.09E-03 1.71E-03 1.94E-03 0.002

ng/dscm@7%O2 9.95E-04 1.57E-03 1.77E-03 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000601 0.00000000458 0.00000000421 0.000

lb/mmBtuO2 4.71E-13 4.93E-13 4.41E-13 0.000

ng/dscm 5.62E-04 5.85E-04 5.26E-04 0.001

ng/dscm@7%O2 5.13E-04 5.37E-04 4.80E-04 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000114 0.000000013 0.0000000151 0.000

lb/mmBtuO2 8.93E-13 1.40E-12 1.58E-12 0.000

ng/dscm 1.07E-03 1.66E-03 1.89E-03 0.002

ng/dscm@7%O2 9.76E-04 1.52E-03 1.73E-03 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000766 0.00000000583 0.00000000537 0.000

lb/mmBtuO2 6.00E-13 6.27E-13 5.62E-13 0.000

ng/dscm 7.16E-04 7.45E-04 6.70E-04 0.001

ng/dscm@7%O2 6.53E-04 6.83E-04 6.12E-04 0.001

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000081 0.00000000866 0.00000000891 0.000

lb/mmBtuO2 6.35E-13 9.32E-13 9.33E-13 0.000

ng/dscm 7.58E-04 1.11E-03 1.11E-03 0.001

ng/dscm@7%O2 6.92E-04 1.02E-03 1.01E-03 0.001

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000975 0.00000000969 0.0000000068 0.000

lb/mmBtuO2 7.64E-13 1.04E-12 7.12E-13 0.000

ng/dscm 9.12E-04 1.24E-03 8.49E-04 0.001

ng/dscm@7%O2 8.32E-04 1.14E-03 7.76E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000302 0.0000000438 0.0000000306 0.000

lb/mmBtuO2 2.37E-12 4.71E-12 3.20E-12 0.000

ng/dscm 2.82E-03 5.60E-03 3.82E-03 0.004

ng/dscm@7%O2 2.57E-03 5.14E-03 3.49E-03 0.004

Monday, February 28, 2011 Page 9 of 25
9/3/2010

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.00000339 0.000002187 0.00000488 0.000

lb/mmBtuO2 2.66E-10 2.35E-10 5.11E-10 0.000

ng/dscm 3.17E-01 2.79E-01 6.09E-01 0.402

ng/dscm@7%O2 2.89E-01 2.56E-01 5.56E-01 0.367

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.0000153 0.0000102 0.0000234 0.000

lb/mmBtuO2 1.20E-09 1.10E-09 2.45E-09 0.000

ng/dscm 1.43E+00 1.30E+00 2.92E+00 1.883

ng/dscm@7%O2 1.30E+00 1.19E+00 2.67E+00 1.720

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000763 0.000000518 0.00000116 0.000

lb/mmBtuO2 5.98E-11 5.57E-11 1.21E-10 0.000

ng/dscm 7.14E-02 6.62E-02 1.45E-01 0.094

ng/dscm@7%O2 6.52E-02 6.07E-02 1.32E-01 0.086

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000257 0.0000177 0.00004 0.000

lb/mmBtuO2 2.01E-09 1.90E-09 4.19E-09 0.000

ng/dscm 2.40E+00 2.26E+00 4.99E+00 3.217

ng/dscm@7%O2 2.19E+00 2.07E+00 4.56E+00 2.940

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.0000011 0.000000749 0.00000168 0.000

lb/mmBtuO2 8.62E-11 8.06E-11 1.76E-10 0.000

ng/dscm 1.03E-01 9.57E-02 2.10E-01 0.136

ng/dscm@7%O2 9.40E-02 8.78E-02 1.92E-01 0.125

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000591 0.000000362 0.000000898 0.000

lb/mmBtuO2 4.63E-11 3.89E-11 9.40E-11 0.000

ng/dscm 5.53E-02 4.63E-02 1.12E-01 0.071

ng/dscm@7%O2 5.05E-02 4.25E-02 1.02E-01 0.065

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000651 0.00000000496 0.00000000456 0.000

lb/mmBtuO2 5.10E-13 5.34E-13 4.77E-13 0.000

Monday, February 28, 2011 Page 10 of 25
9/3/2010

ng/dscm 6.09E-04 6.34E-04 5.69E-04 0.001

ng/dscm@7%O2 5.56E-04 5.82E-04 5.20E-04 0.001

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000101 0.00000001 0.00000000703 0.000

lb/mmBtuO2 7.91E-13 1.08E-12 7.36E-13 0.000

ng/dscm 9.45E-04 1.28E-03 8.78E-04 0.001

ng/dscm@7%O2 8.62E-04 1.17E-03 8.02E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000739 0.00000000625 0.00000000929 0.000

lb/mmBtuO2 5.79E-13 6.72E-13 9.72E-13 0.000

ng/dscm 6.91E-04 7.99E-04 1.16E-03 0.001

ng/dscm@7%O2 6.31E-04 7.33E-04 1.06E-03 0.001

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000805 0.0000000075 0.00000000561 0.000

lb/mmBtuO2 6.31E-13 8.07E-13 5.87E-13 0.000

ng/dscm 7.53E-04 9.58E-04 7.00E-04 0.001

ng/dscm@7%O2 6.87E-04 8.79E-04 6.39E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000488 0.0000000887 0.00000004 0.000

lb/mmBtuO2 3.82E-12 9.54E-12 4.19E-12 0.000

ng/dscm 4.56E-03 1.13E-02 4.99E-03 0.007

ng/dscm@7%O2 4.16E-03 1.04E-02 4.56E-03 0.006

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000667 0.0000000879 0.000000169 0.000

lb/mmBtuO2 5.23E-12 9.46E-12 1.77E-11 0.000

ng/dscm 6.24E-03 1.12E-02 2.11E-02 0.013

ng/dscm@7%O2 5.69E-03 1.03E-02 1.93E-02 0.012

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000487 0.000000363 0.000000676 0.000

lb/mmBtuO2 3.82E-11 3.91E-11 7.08E-11 0.000

ng/dscm 4.55E-02 4.64E-02 8.44E-02 0.059

ng/dscm@7%O2 4.15E-02 4.26E-02 7.71E-02 0.054

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Monday, February 28, 2011 Page 11 of 25
9/3/2010

Mass_mg 0.0000000393 0.000000254 0.0000000391 0.000

lb/mmBtuO2 3.08E-12 2.73E-11 4.09E-12 0.000

ng/dscm 3.68E-03 3.25E-02 4.88E-03 0.014

ng/dscm@7%O2 3.36E-03 2.98E-02 4.46E-03 0.013

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000224 0.000000027 0.0000000195 0.000

lb/mmBtuO2 1.75E-12 2.90E-12 2.04E-12 0.000

ng/dscm 2.10E-03 3.45E-03 2.43E-03 0.003

ng/dscm@7%O2 1.92E-03 3.16E-03 2.22E-03 0.002

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000135 0.000000025 0.0000000197 0.000

lb/mmBtuO2 1.06E-12 2.69E-12 2.06E-12 0.000

ng/dscm 1.26E-03 3.19E-03 2.46E-03 0.002

ng/dscm@7%O2 1.15E-03 2.93E-03 2.25E-03 0.002

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Monday, February 28, 2011 Page 12 of 25
9/3/2010

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.00000006031 0.00000005774 0.00000006218 0.000

lb/mmBtuO2 4.72E-12 6.21E-12 6.51E-12 0.000

ng/dscm 5.64E-03 7.38E-03 7.76E-03 0.007

ng/dscm@7%O2 5.15E-03 6.77E-03 7.09E-03 0.006

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.00000004621 0.00000005638 0.0000000437 0.000

lb/mmBtuO2 3.62E-12 6.07E-12 4.57E-12 0.000

ng/dscm 4.32E-03 7.20E-03 5.46E-03 0.006

ng/dscm@7%O2 3.94E-03 6.60E-03 4.99E-03 0.005

Compound: Total Mono-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

Monday, February 28, 2011 Page 13 of 25
9/3/2010

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Nona-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Octa-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total PCBs

Average

RunNumber 1 2 3

Mass_mg 0.000189 0.000137 0.000308 0.000

lb/mmBtuO2 1.48E-08 1.47E-08 3.22E-08 0.000

ng/dscm 1.77E+01 1.75E+01 3.85E+01 24.567

ng/dscm@7%O2 1.62E+01 1.61E+01 3.52E+01 22.500

Compound: Total PeCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total PeCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Penta-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total TCDD

Average

RunNumber 1 2 3

Monday, February 28, 2011 Page 14 of 25
9/3/2010

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total TCDF 

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0.0000261 0.0000254 0.0000000279 0.000

lb/mmBtuO2 2.04E-09 2.73E-09 2.92E-12 0.000

ng/dscm 2.44E+00 3.25E+00 3.48E-03 1.898

ng/dscm@7%O2 2.23E+00 2.98E+00 3.18E-03 1.738

Compound: Total Tetra-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Tri-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 2.5 2.6 2.7 2.600

Elb/hr 1.58E+01 1.63E+01 1.69E+01 16.333

lb/mmBtuO2 2.14E-03 2.05E-03 2.18E-03 0.002

mg/dscm 2.43E+00 2.50E+00 2.63E+00 2.520

mg/dscm@7%O2 2.33E+00 2.23E+00 2.37E+00 2.310

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 2.6 2.7 2.7 2.667

Elb/hr 1.64E+01 1.69E+01 1.69E+01 16.733

lb/mmBtuO2 2.22E-03 2.13E-03 2.18E-03 0.002

Monday, February 28, 2011 Page 15 of 25
9/3/2010

mg/dscm 2.52E+00 2.60E+00 2.63E+00 2.583

mg/dscm@7%O2 2.42E+00 2.32E+00 2.37E+00 2.370

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.0006 0.0006 0.0006 0.001

Elb/hr 9.51E-04 9.53E-04 9.46E-04 0.001

lb/mmBtuO2 1.20E-07 1.18E-07 1.20E-07 0.000

mg/dscm 1.43E-04 1.44E-04 1.43E-04 0.000

mg/dscm@7%O2 1.31E-04 1.29E-04 1.31E-04 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.0006 0.00061 0.0006 0.001

Elb/hr 9.51E-04 9.69E-04 9.46E-04 0.001

lb/mmBtuO2 1.20E-07 1.20E-07 1.20E-07 0.000

mg/dscm 1.43E-04 1.47E-04 1.43E-04 0.000

mg/dscm@7%O2 1.31E-04 1.31E-04 1.31E-04 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.0003 0.0003 0.0003 0.000

Elb/hr 4.76E-04 4.76E-04 4.73E-04 0.000

lb/mmBtuO2 6.01E-08 5.92E-08 6.02E-08 0.000

mg/dscm 7.17E-05 7.22E-05 7.17E-05 0.000

mg/dscm@7%O2 6.56E-05 6.45E-05 6.56E-05 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0003 0.0003 0.0003 0.000

Elb/hr 4.76E-04 4.76E-04 4.73E-04 0.000

lb/mmBtuO2 6.01E-08 5.92E-08 6.02E-08 0.000

mg/dscm 7.17E-05 7.22E-05 7.17E-05 0.000

mg/dscm@7%O2 6.56E-05 6.45E-05 6.56E-05 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.00139 0.00109 0.0008 0.001

Elb/hr 2.20E-03 1.73E-03 1.26E-03 0.002

lb/mmBtuO2 2.79E-07 2.15E-07 1.60E-07 0.000

mg/dscm 3.32E-04 2.62E-04 1.91E-04 0.000

mg/dscm@7%O2 3.04E-04 2.34E-04 1.75E-04 0.000

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

Monday, February 28, 2011 Page 16 of 25
9/3/2010

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

mg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

mg/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.00064 0.00068 0.00062 0.001

Elb/hr 1.01E-03 1.08E-03 9.78E-04 0.001

lb/mmBtuO2 1.28E-07 1.34E-07 1.24E-07 0.000

mg/dscm 1.53E-04 1.64E-04 1.48E-04 0.000

mg/dscm@7%O2 1.40E-04 1.47E-04 1.35E-04 0.000

Compound: Magnesium

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

mg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

mg/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0108 0.01064 0.00658 0.009

Elb/hr 1.71E-02 1.69E-02 1.04E-02 0.015

lb/mmBtuO2 2.17E-06 2.10E-06 1.32E-06 0.000

mg/dscm 2.58E-03 2.56E-03 1.57E-03 0.002

mg/dscm@7%O2 2.36E-03 2.29E-03 1.44E-03 0.002

Compound: Mercury

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

mg/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

mg/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.00429 0.0023 0.00172 0.003

Elb/hr 6.80E-03 3.65E-03 2.71E-03 0.004

lb/mmBtuO2 8.60E-07 4.54E-07 3.45E-07 0.000

mg/dscm 1.02E-03 5.54E-04 4.11E-04 0.001

mg/dscm@7%O2 9.33E-04 4.95E-04 3.76E-04 0.001

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.00153 0.0019 0.00147 0.002

Monday, February 28, 2011 Page 17 of 25
9/3/2010

Process Run Data

Elb/hr 2.43E-03 3.02E-03 2.32E-03 0.003

lb/mmBtuO2 3.07E-07 3.75E-07 2.95E-07 0.000

mg/dscm 3.65E-04 4.57E-04 3.51E-04 0.000

mg/dscm@7%O2 3.34E-04 4.08E-04 3.21E-04 0.000

Location: Stack Exit - Method 5/OTM-28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 12.27 28.79 9.21 16.757

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 10.82 6.91 20.24 12.657

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 0.83 0.99 1.62 1.147

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 23.92 36.69 31.07 30.560

Monday, February 28, 2011 Page 18 of 25
9/3/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Coal Firing Rate 0 0

2 Coal Firing Rate 0 0

3 Coal Firing Rate 0 0

1 Average Heat Input 0 MMBtu/hr 0

2 Average Heat Input 0 MMBtu/hr 0

3 Average Heat Input 0 MMBtu/hr 0

1 Steam Output 0 1000 lb steam/hr 0

2 Steam Output 0 1000 lb steam/hr 0

3 Steam Output 0 1000 lb steam/hr 0

1 Synfuel Firing Rate 0 0

2 Synfuel Firing Rate 0 0

3 Synfuel Firing Rate 0 0

1 Petroleum Coke Firing Rate 0 0

2 Petroleum Coke Firing Rate 0 0

3 Petroleum Coke Firing Rate 0 0

1 Coal Gas Firing Rate 0 0

2 Coal Gas Firing Rate 0 0

3 Coal Gas Firing Rate 0 0

1 Fuel Oil Firing Rate 0 0

2 Fuel Oil Firing Rate 0 0

3 Fuel Oil Firing Rate 0 0

1 Flue Gas Flow Rate 0 dscfm 0

1 Pressure Drop Across FGD (if applicable) 0 in H20 0

1 FGD Scrubber Liquor pH 0 pH 0

1 FGD Scrubber Liquor Flow Rate 0 gal/min 0

1 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

1 Flue Gas Oxygen Content 0 % 0

1 Flue Gas Carbon Dioxide Content 0 % 0

1 Flue Gas Moisture Content 0 % 0

1 Flue Gas Sampling Point Temperature 0 Deg F 0

1 Flue Gas Pressure 0 atm 0

1 Standard Pressure 0 atm 0

1 Standard Temperature 0 Deg F 0

Monday, February 28, 2011 Page 19 of 25
9/3/2010

APCD Run Data

Process Lab Run Data

1 Unit Gross Electrical Output 0 MW 0

1 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

Target

Value

1 OVERFIRE AIR 0 0

1 ELECTROSTATIC PRECIPITATOR 0 0

1 WET SCRUBBER 0 0

Run Name Value UOM Comments

1 Fuel Higher Heating Value 0 Btu/lb

1 Fuel Moisture 0 %

1 Fuel Mercury Content 0 ppm

1 Fuel Cadmium Content 0 ppm

1 Ultimate/Proximate Analysis 0

1 Fuel Nickel Content 0 ppm

1 Fuel Arsenic Content 0 ppm

1 Fuel Chromium Content 0 ppm

1 Fuel Beryllium Content 0 ppm

1 Fuel Lead Content 0 ppm

1 Fuel Manganese Content 0 ppm

1 Fuel Chlorine Content 0 ppm

1 Fuel Fluorine Content 0 ppm

Monday, February 28, 2011 Page 20 of 25
9/3/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 1 - 4

Average

Run Number 1 2 3

Test Date 3/24/2010 3/25/2010 3/25/2010

Run Start Time 11:53:00 AM 7:20:00 AM 2:17:00 PM

Run Finish Time 4:19:00 PM 11:51:00 AM 6:28:00 PM

Net Traversing Points 12 12 12

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.215 0.215 0.215 0.215

Pitot Tube Coefficient 0.8093 0.8093 0.8093 0.809

Dry Gas Meter Calibration Factor 0.984 0.984 0.984 0.984

Barometric Pressure, inches of Mercury 29.58 29.41 29.41 29.467

Average Orifice Meter Differential, inches H2O 1.44 1.46 1.51 1.470

Dry Gas Meter Volume Sampled, cubic feet 158.723 157.670 164.783 160.392

Average Dry Gas Meter Temperature, °F 85.08 81.08 80.58 82.247

Dry Gas Meter Volume Sampled, dscf 150.106 149.359 156.261 151.909

Total Moisture Liquid collected, g 586.1 692.2 723.3 667.200

Volume of Water Vapor, standard cubic feet 27.59 32.58 34.05 31.407

Moisture Content of Stack Gas, % 15.53 17.91 17.89 17.110

Moisture Saturation at Stack Gas Temperature, % 16.27 16.26 16.32 16.283

Dry Mole Fraction 0.8447 0.8374 0.8368 0.840

Carbon Dioxide, % 14.098 13.798 13.929 13.942

Oxygen, % 5.392 5.733 5.612 5.579

Carbon Monoxide & Nitrogen, % 80.51 80.469 80.459 80.479

Fuel Factor 1.10 1.10 1.10

Dry Molecular Weight, lb/lb-Mole 30.47 30.44 30.45 30.453

Wet Molecular weight, lb/lb-Mole 28.53 28.71 28.70 28.647

Flue Gas Static Pressure, inches of H2O -0.48 -0.49 -0.44 -0.470

Absolute Flue Gas Pressure, inches of Mercury 29.54 29.37 29.38 29.430

Average Stack Gas Temperature, °F 132.33 132.08 132.25 132.220

Average Velocity Head, inches of H2O 0.9557159877

63746

0.970491330

492534

0.913595075

452909

0.947

Average Stack Gas Velocity, feet/second 56.70 57.11 55.42 56.410

Stack Cross-Sectional Area, square feet 695.126 695.126 695.126 695.126

Dry Volumetric Flow Rate, dry scfm 1,758,002.3 1,746,046.4 1,693,253.7 1,732,434.1

33

Actual Wet Volumetric Flue Gas Flow Rate, acfm 2,364,818.7 2,381,918.8 2,311,433.0 2,352,723.5

00

Percent Isokinetic of Sampling Rate, % 98.1 98.3 106.0 100.800

Percent Excess Air, % 34.0 37.0 35.9 35.633

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Round Duct Diameter, inches 357 357 357

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Monday, February 28, 2011 Page 21 of 25
9/3/2010

Location Stack Exit - Method 23

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 28, 2011 Page 22 of 25
9/3/2010

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 28, 2011 Page 23 of 25
9/3/2010

Location Stack Exit - Method 29 

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 28, 2011 Page 24 of 25
9/3/2010

Location Stack Exit - Method 5/OTM-28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Monday, February 28, 2011 Page 25 of 25