Facility _Information facility _id utility

_code legal_owner_nam e

legl_operator_name

legal_address_type

legal_address

legal_city legal_state legal_zip 1720 4254 Consumers Energy Co. Consumers Energy

Co. legal ownerOne Energy Plaza Jackson MI 49201

Page 1Facility _Information plant_nam e

physical_address

phyical_city

physical_state

physical_zip

mailing_address

mailing_city

mailing_state

mailing_zip J.C. Weadock

2555 N. Weadock Hwy
.

Essexville MI 48732 2555 N. Weadock Hwy
. Essexville MI 48732

Page 2Facility _Information RFA_small_entity

ff_fired_coal

ff_fired_oil ff_fired_ngas ff_fired_petcoke

ff_fired_other

ff_permitted_coal

ff_permitted_oil

ff_permitted_ngas No TRUE TRUE FALSE FALSE FALSE TRUE TRUE FALSE

Page 3Facility _Information ff_permitted_petcoke

ff_permitted_other

deviation_reporting

continuous_emissions

cem_provided

facility _note FALSE FALSE Prompt deviation reporting, semi-annual ROP deviation reporting No PART IFacility and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 4Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 5Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 6Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 7Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 8Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 9Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 10Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 11Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 12Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 13Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 14Facility _Information PART IFacility

and Fuel InformationUnit 7& 8:Oil burned for start-up operation and flame stabilizationFacility Unit Configurations1) If month of control installation was not known, then the month of December was used.2) For Question 16 of ICR, planned control equipment includes:Unit 7 - Low Nox burner installation, in service 2010Unit 8 - Low Nox burner installation, in service 2010Boiler InformationTemperatures above 300F were not allowed by the software to be entered in the database. EPA guidance directed to enter "1" and then put in to the Notes section.Unit 7-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9645 Btu/lbmDesign steam temperature (F)1050FOperating steam temperature(F) 1038FDesign reheat Temperature (F) 1000FOperating reheat temperature(F) 992FUnit 8-original design gross efficiency (HHV) 11,000 Btu/lbmpresent operating gross efficiency (HHV)9731 Btu/lbmDesign steam temperature (F)1050FOperating s

Page 15facility _contacts facility _id contact_id contact_title contact_name

contact_phone1

contact_phone2

contact_email

contact_primary 1720 1 Project Engineer Corwin Holm es

5177881756 clholmes@cmsenergy.com FALSE 1720 2 Sr. Environmental Planner Katie Cunningham

5177683468 kmcunningham@cmsenergy.com TRUE

Page 16facility _coal_utilized facility _id coal_type percentage_mass percentage_btu

synfuel_type

coal_note 1720 bitum inous 25 32.4 Applicabble to Unit 7 and Unit 8Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800 1720 subbituminous 75 67.6 Applicabble to Unit 7 and Unit 8Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800

Page 17facility _coal_utilized Applicabble to Unit 7 and Unit 8Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800 Applicabble to Unit 7 and Unit 8Assumed Bituminous coal btu/lb content :12650Assumed subbituminous coal btu/lb content:8800

Page 18facility _oil_utilized facility _id oil_type percentage_volume percentage_btu

other_type 1720 No.2 Fuel Oil (distillate) 100 100

Page 19facility _other_materials facility _id other_material

permitted_burn

actually _burn other_quantity

other_quantity

_units other_note rcra_utilize rcra_explain

Page 20facility _other_materials rcra_explain

Page 21boiler_information

facility _id boiler_id boiler_type boiler_other bottom_design

design_fuelheat_input max_heat_input MWe_capacity 1720 7 Tangential firing Wet Bottom coal 1378.3 1560 166 1720 8 Tangential firing Wet Bottom coal 1378.3 1475 166.5

Page 22boiler_information

MWe_net_capacity

design_gross_efficiency

operating_gross_efficiency

design_pressure

operating_pressure

design_temp

operating_temp

design_reheat_multiple

design_reheat_temp1 155 89.33 86.1 2000 2007 1 1 FALSE 155 89.33 86.9 2000 2004 FALSE

Page 23boiler_information

design_reheat_temp2

operating_reheat_multiple

operating_reheat_temp1

operating_reheat_temp2

hours_operated

vg_capacity

_factor applicable_NSPS

retirement_year

retirement_year_CBI FALSE 7947 75.97 N 2025 FALSE FALSE 7109 44.55 N 2025 FALSE

Page 24boiler_information

NOx_control

SO2_control

combustion_additives No Yes No Yes Yes No

Page 25boiler_fuels

facility _id boiler_id fuel_type fuel_year percentage_massvol percentage_btu

other_type 1720 7 coal - bituminous2009 25 32.4 1720 7 coal - subbituminous 2009 75 67.6 1720 8 coal - bituminous2009 25 32.4 1720 8 coal - subbituminous 2009 75 67.6

Page 26boiler_control_NOx

facility _id boiler_id NOx_type NOx_other NOx_online 1720 8 Low NOx Burner 3/1/2010

Page 27boiler_control_SO2

facility _id boiler_id SO2_type SO2_other SO2_online 1720 7 Low Sulfur Coal 12/1/1980 1720 8 Low Sulfur Coal 12/1/1980

Page 28boiler_additives

facility _id boiler_id boiler_additive additive_other

additive_online

Page 29facility _units facility _id unit_id 1720 Unit 7 1720 Unit 8

Page 30unit_boilers

facility _id unit_id boiler_id 1720 Unit 7 7 1720 Unit 8 8

Page 31facility _controls facility _id control_id control_group control_type

control_other

legacy _control cntrol_online

control_offline

NOx_reagent 1720 JCW 7-ESPPM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 12/1/1971 1720 JCW8-ESPPM control Electrostatic precipitator, cold side, w/ flue gas conditioning FALSE 12/1/1971

Page 32facility _controls reagent_other

NOx_ammonia

SO2_sorbent

oher_sorbent

SO2_scrubber_additive

Page 33facility _sampling_ports facility _id sampling_port_id 1720 JCW 7-Port 1720 JCW8-Port

Page 34facility _stacks facility _id stack_id stack_height stack_diameter

sack_gas_velocity 1720 JCW 78 Stack 498 17

Page 35configurations

facility _id configuration_id 1720 JCW 7-Conf 1720 JCW8-Conf

Page 36configuration_components

facility _id configuration_id

component_id

order component_type port_near 1720 JCW 7-Conf

JCW 78 Stack 4 Stack 1720 JCW 7-Conf

JCW 7-ESP 2 PM control 1720 JCW 7-Conf

JCW 7-Port 3 Sam pling Port 1720 JCW 7-Conf

Unit 7 1 Unit 1720 JCW8-Conf

JCW 78 Stack 4 Stack 1720 JCW8-Conf

JCW8-ESP 2 PM control 1720 JCW8-Conf

JCW8-Port 3 Sam pling Port 1720 JCW8-Conf

Unit 8 1 Unit

Page 37configuration_pollutants1

facility _id configuration_id

pollutant_nam e

permit_type_1

em lim it_1 em lim it_units_1 avg_period_1

em lim it_2 em lim it_units_2 1720 JCW 7-Conf

PM (Filterable)

Fderal - Title V Operating Permit

0.18 1 hour 1720 JCW 7-Conf

Sulfur Dioxide (SO2)

Federal - Title V Operating Permit

1.67 pound per million British Thermal Unit (lb/MMBtu)

30 days 1720 JCW8-Conf

PM (Filterable)

Fderal - Title V Operating Permit

0.18 1 hour 1720 JCW8-Conf

Sulfur Dioxide (SO2)

Federal - Title V Operating Permit

1.67 pound per million British Thermal Unit (lb/MMBtu)

30 days

Page 38configuration_pollutants1

avg_period_2

em lim it_details

test_method

em rate em rate_units guarantee_level

_explain

req_monitoring

eq_recordkeeping lbs/1000 lbs exhaust gas, 50% air

Method 17 Stack Test, COMs Stack Test Report, COMs six minute averages CEMs CEMs in accordance with Part 75, monthly calendar average emission rate lbs/1000 lbs exhaust gases

Method 17 Stack Test, COMs Stack Test Report, COMs six minute averages CEMs CEMs informaiton according to Part 75, monthly calendar average emission rate

Page 39configuration_pollutants1

req_reporting Stack Test Reports, COMs excursion reporting, Quarterly EER, Sem i-annual m onitoring deviations, Sem i-annual ROP deviations Quarterly

EER, Sem i-annual m onitoring deviations, Sem i-annual ROP deviations Stack Test Reports, COMs excursion reporting, Quarterly EER, Sem i-annual m onitoring deviations, Sem i-annual ROP deviations Quarterly

EER, Sem i-annual m onitoring deviations, Sem i-annual ROP deviations

Page 40configuration_pollutants1 Stack Test Reports, COMs excursion reporting, Quarterly EER, Sem i-annual m onitoring deviations, Sem i-annual ROP deviations Stack Test Reports, COMs excursion reporting, Quarterly EER, Sem i-annual m onitoring deviations, Sem i-annual ROP deviations

Page 41control_technologies

facility _id configuration_id

component_id

control_id project_titleproject_type vendor_name

vndor_contact

vendor_phone

Page 42control_technologies

vendor_address

vndor_city

vendor_state

vendor_zip actual_start_date projected_start_date

end_date sorbent chemical_additive

Page 43control_technologies

injection_point

HAP_em ission_reduction

HAP_em ission_rate

HAP_em ission_rate_units

HAP_achieved_reduction

HAP_achieved_rate

HAP_achieved_rate_units

feed_rate feed_rate_units

Page 44control_technologies feed_rate_units

Page 45control_coal_ranks

facility _id configuration_id

component_id

control_id coal_type

Page 46control_pollutants1

facility _id configuration_id

component_id

control_id pollutant_nam e

Page 47control_costs

facility _id configuration_id

component_id

control_id boiler_retrofit boiler_new_install

total_capital_investm ent

total_operating_costs

base_year

Page 48control_costs

CBI

Page 49misc_controls

facility _id misc_control_id

control_description

Page 50misc_control_configurations

facility _id misc_control_id

configuration_id

Page 51fuel_shipments

facility _id shipment_id

shipment_date

am ount_received

am ount_units

fuel_type state_country other_country

county 1720 AY 1/1/2009 34487.21 short tons (2000 lbs) coal WY 1720 AZ 2/1/2009 37176.8 short tons (2000 lbs) coal WY 1720 BA 3/1/2009 58427.25 short tons (2000 lbs) coal WY 1720 BB 4/1/2009 68345.71 short tons (2000 lbs) coal WY 1720 BC 5/1/2009 28906.09 short tons (2000 lbs) coal WY 1720 BD 6/1/2009 68575.27 short tons (2000 lbs) coal MT 1720 BE 7/1/2009 68096.72 short tons (2000 lbs) coal MT 1720 BF 8/1/2009 67357 short tons (2000 lbs) coal MT 1720 BG 9/1/2009 68183.84 short tons (2000 lbs) coal MT 1720 BH 10/1/2009 82809.55 short tons (2000 lbs) coal MT 1720 BI 11/1/2009 22402.65 short tons (2000 lbs) coal MT 1720 BJ 12/1/2009 22289.18 short tons (2000 lbs) coal MT 1720 CP 1/1/2009 19688.9 short tons (2000 lbs) coal WV 1720 CQ 2/1/2009 51246.33 short tons (2000 lbs) coal WV 1720 CR 3/1/2009 50483.2 short tons (2000 lbs) coal WV 1720 CS 4/1/2009 85200.5 short tons (2000 lbs) coal WV 1720 CT 5/1/2009 53500.4 short tons (2000 lbs) coal WV 1720 CU 6/1/2009 42956.23 short tons (2000 lbs) coal WV 1720 CV 7/1/2009 32593.26 short tons (2000 lbs) coal WV 1720 CW 8/1/2009 31592.38 short tons (2000 lbs) coal WV 1720 CX 9/1/2009 52624.52 short tons (2000 lbs) coal WV 1720 CY 10/1/2009 41414.42 short tons (2000 lbs) coal WV 1720 CZ 12/1/2009 44295.72 short tons (2000 lbs) coal WV 1720 DecNo2 12/1/2009 319 barrels oil MI 1720 FebNo2 2/1/2009 319 barrels oil MI 1720 JanNo2 1/1/2009 333 barrels oil MI 1720 MarNo2 3/1/2009 1428 barrels oil MI 1720 MayNo2 5/1/2009 357 barrels oil MI 1720 NovNo2 11/1/2009 357 barrels oil MI 1720 OctNo2 10/1/2009 319 barrels oil MI 1720 SepNo2 9/1/2009 357 barrels oil MI

Page 52fuel_shipments

coal_seam shipment_method

Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Ship Ship Ship Ship Ship Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Unit Train Trucks Trucks Trucks Trucks Trucks Trucks Trucks Trucks

Page 53fuel_shipment_configurations

facility _id shipment_id

configuration_id 1720 AY JCW 7-Conf 1720 AY JCW8-Conf 1720 AZ JCW 7-Conf 1720 AZ JCW8-Conf 1720 BA JCW 7-Conf 1720 BA JCW8-Conf 1720 BB JCW 7-Conf 1720 BB JCW8-Conf 1720 BC JCW 7-Conf 1720 BC JCW8-Conf 1720 BD JCW 7-Conf 1720 BD JCW8-Conf 1720 BE JCW 7-Conf 1720 BE JCW8-Conf 1720 BF JCW 7-Conf 1720 BF JCW8-Conf 1720 BG JCW 7-Conf 1720 BG JCW8-Conf 1720 BH JCW 7-Conf 1720 BH JCW8-Conf 1720 BI JCW 7-Conf 1720 BI JCW8-Conf 1720 BJ JCW 7-Conf 1720 BJ JCW8-Conf 1720 CP JCW 7-Conf 1720 CP JCW8-Conf 1720 CQ JCW 7-Conf 1720 CQ JCW8-Conf 1720 CR JCW 7-Conf 1720 CR JCW8-Conf 1720 CS JCW 7-Conf 1720 CS JCW8-Conf 1720 CT JCW 7-Conf 1720 CT JCW8-Conf 1720 CU JCW 7-Conf 1720 CU JCW8-Conf 1720 CV JCW 7-Conf 1720 CV JCW8-Conf 1720 CW JCW 7-Conf 1720 CW JCW8-Conf 1720 CX JCW 7-Conf 1720 CX JCW8-Conf 1720 CY JCW 7-Conf 1720 CY JCW8-Conf 1720 CZ JCW 7-Conf 1720 CZ JCW8-Conf 1720 DecNo2 JCW 7-Conf 1720 DecNo2 JCW8-Conf 1720 FebNo2 JCW 7-Conf 1720 FebNo2 JCW8-Conf 1720 JanNo2 JCW 7-Conf Page 54fuel_shipment_configurations

1720 JanNo2 JCW8-Conf 1720 MarNo2 JCW 7-Conf 1720 MarNo2 JCW8-Conf 1720 MayNo2 JCW 7-Conf 1720 MayNo2 JCW8-Conf 1720 NovNo2 JCW 7-Conf 1720 NovNo2 JCW8-Conf 1720 OctNo2 JCW 7-Conf 1720 OctNo2 JCW8-Conf 1720 SepNo2 JCW 7-Conf 1720 SepNo2 JCW8-Conf

Page 55fuel_shipment_samples

facility _id shipment_id

sample_id am ount_fuel am ount_fuel_units

total_sulfur ash_content heating_value

hating_units

Page 56fuel_shipment_samples

chlorine chlorine_units fluorine fluorine_units data_provided

data_other_specified

supplier_type

supplier_name

supplier_address

Page 57fuel_shipment_samples

supplier_city

supplier_state

supplier_zip

lab_nam e lab_address lab_city lab_state lab_zip analysis_copies

Page 58fuel_shipment_samples analysis_copies

Page 59fuel_sample_pollutants

facility _id shipment_id

sample_id fuel_pollutant pollutant_conc

pollutant_conc_units

pollutant_conc_ND

pollutant_conc_MDL

Page 60test_reports

facility _id report_id report_type other_type report_description report_begin_date

report_end_date

before_control

during_deviation 1720 2005-JCW 8 PM Testing

compliance Particulate testing required by ROP ######## No No 1720 2008-JCW 8

compliance Particulate testing required in ROP 3/13/2008 No No 1720 JCW 7-2005 PM Testing

compliance Particulate testing required by ROP ######## ######## No No 1720 JCW 7-2008 PM Testing

compliance Particulate testing required by ROP 3/12/2008 No No 1720 JCW 78 - Hg CEMs Performance Test

other Vendor Guarentee Performance Testing RATA for Hg CEMs for vendor performance guarentee for engineering project.

######## ######## No No

Page 61test_reports

deviation_reports No No No No No

Page 62test_report_configurations

facility _id report_id configuration_id 1720 2005-JCW 8 PM Testing

JCW8-Conf 1720 2008-JCW 8

JCW8-Conf 1720 JCW 7-2005 PM Testing

JCW 7-Conf 1720 JCW 7-2008 PM Testing

JCW 7-Conf 1720 JCW 78 - Hg CEMs Performance Test

JCW 7-Conf 1720 JCW 78 - Hg CEMs Performance Test

JCW8-Conf

Page 63test_report_fuels

facility _id report_id fuel_id 1720 2005-JCW 8 PM Testing

coal 1720 2008-JCW 8

coal 1720 JCW 7-2005 PM Testing

coal 1720 JCW 7-2008 PM Testing

coal 1720 JCW 78 - Hg CEMs Performance Test

coal

Page 64test_report_fuel_types

facility _id report_id fuel_id fuel_type percentage_massvol percentage_btu

other_type

Page 65cem_data

facility _id tim e_period

cem_period_description 1720 2005-2009

Page 66cem_data_pollutants1

facility _id tim e_period

pollutant_nam e 1720 2005-2009 Sulfur Dioxide (SO2) 1720 2005-2009 Nitrogen Oxide (NOx)

Page 67test_report_sampling

facility _id report_id sampling_port_id point_differ point_description befre_SO2_device

point_orientation

normal_bypass_percent

testing_bypass_percent 1720 2005-JCW 8 PM Testing

JCW8-Port No No 1720 2008-JCW 8

JCW8-Port No No 1720 JCW 7-2005 PM Testing

JCW 7-Port No No 1720 JCW 7-2008 PM Testing

JCW 7-Port No No 1720 JCW 78 - Hg CEMs Performance Test

JCW 78 Stack

No No

Page 68test_report_sampling

fg_fraction

Page 69sampling_runs

facility _id report_id sampling_port_id run_id start_datetime end_datetim e

unit_load net_generation fg_moisture_content 1720 2005-JCW 8 PM Testing

JCW8-Port 1 ######## ######## 161 10.6 1720 2005-JCW 8 PM Testing

JCW8-Port 2 ######## ######## 160 10.2 1720 2005-JCW 8 PM Testing

JCW8-Port 3 ######## ######## 160 11.4 1720 2005-JCW 8 PM Testing

JCW8-Port average ######## ######## 160 10.7 1720 2008-JCW 8

JCW8-Port 1 3/13/2008 3/13/2008 154 10.6 1720 2008-JCW 8

JCW8-Port 2 3/14/2008 3/14/2008 157 10.9 1720 2008-JCW 8

JCW8-Port 3 3/14/2008 3/14/2008 156 11.9 1720 2008-JCW 8

JCW8-Port average 3/13/2008 3/14/2008 156 10.8 1720 JCW 7-2005 PM Testing

JCW 7-Port 1 ######## ######## 161 10.6 1720 JCW 7-2005 PM Testing

JCW 7-Port 2 ######## ######## 161 10.4 1720 JCW 7-2005 PM Testing

JCW 7-Port 3 ######## ######## 168 11.9 1720 JCW 7-2005 PM Testing

JCW 7-Port average ######## ######## 156 11 1720 JCW 7-2008 PM Testing

JCW 7-Port 1 3/12/2008 3/12/2008 157 10.7 1720 JCW 7-2008 PM Testing

JCW 7-Port 2 3/12/2008 3/12/2008 156 11.5 1720 JCW 7-2008 PM Testing

JCW 7-Port 3 3/13/2008 3/13/2008 156 11.2 1720 JCW 7-2008 PM Testing

JCW 7-Port average 3/12/2008 3/13/2008 156 11.1 1720 JCW 78 - Hg CEMs Performance Test

JCW 78 Stack

average ######## ########

Page 70sampling_runs

fg_flow_rate

fg_flow_rate_units

standard_temperature

standard_pressure

normal_temperature

normal_pressure

fg_oxygen_content

fg_CO2_content

fg_temperature 380427 dscfm 4.6 15.02 294 380916 dscfm 4.62 14.93 298 385522 dscfm 4.38 14.88 1 382288 dscfm 4.53 14.94 297 342599 dscfm 4.12 14.92 288.8 361781 dscfm 4.03 15.17 285.8 345238 dscfm 4.18 14.96 288 349873 dscfm 4.11 15.02 287.5 363186 dscfm 3.83 15.56 1 357509 dscfm 3.84 15.5 1 372271 dscfm 3.94 15.39 1 364322 dscfm 3.87 15.48 1 354427 dscfm 4.07 15.19 1 351981 dscfm 4.04 15.38 1 349637 dscfm 3.95 15.06 1 352015 dscfm 4.02 15.21 1

Page 71sampling_runs

fg_pressure

Hg_loi test_method run_comments

fuel_id fuel_unit_load fuel_flow_rate

fuel_ash fuel_heating_value 17 12244 17 12244 17 flue gas temp=300F 12269 17 12252 17 12576 17 12317 17 12204 17 12366 17 flue gas temp=303F 12353 17 flue gas temp=303F 12286 17 flue gas temp=304F 13326 Method 17 Stack Temp was 303F 12655 17 flue gas temp=308.6F 12372 17 flue gas temp=307.9 12064 17 flue gas temp=309.9 12289 Method 17 Flue Gase Temp was 308.8F 12242 30B

Page 72sampling_runs

fuel_sulfur

Page 73sampling_run_pollutants1

facility _id report_id sampling_port_id run_id pollutant_nam e conc conc_units conc_ND conc_MDL 1720 JCW 7-2008 PM Testing

JCW 7-Port 3 PM (Filterable) 0.0577 FALSE 1720 2008-JCW 8

JCW8-Port 1 PM (Filterable) 0.0992 FALSE 1720 2008-JCW 8

JCW8-Port 2 PM (Filterable) 0.0776 FALSE 1720 2008-JCW 8

JCW8-Port 3 PM (Filterable) 0.0699 FALSE 1720 2008-JCW 8

JCW8-Port average PM (Filterable) 0.0822 FALSE 1720 2005-JCW 8 PM Testing

JCW8-Port 1 PM (Filterable) 0.0525 FALSE 1720 2005-JCW 8 PM Testing

JCW8-Port 2 PM (Filterable) 0.0313 FALSE 1720 2005-JCW 8 PM Testing

JCW8-Port 3 PM (Filterable) 0.0275 FALSE 1720 2005-JCW 8 PM Testing

JCW8-Port average PM (Filterable) 0.0371 FALSE 1720 JCW 7-2008 PM Testing

JCW 7-Port average PM (Filterable) 0.0489 FALSE 1720 JCW 7-2005 PM Testing

JCW 7-Port average PM (Filterable) 0.0406 FALSE 1720 JCW 78 - Hg CEMs Performance Test

JCW 78 Stack

average Total Mercury (Hgt) 2.314 FALSE 1720 JCW 7-2005 PM Testing

JCW 7-Port 1 PM (Filterable) 0.0641 FALSE 1720 JCW 7-2005 PM Testing

JCW 7-Port 2 PM (Filterable) 0.0208 FALSE 1720 JCW 7-2005 PM Testing

JCW 7-Port 3 PM (Filterable) 0.0369 FALSE 1720 JCW 7-2008 PM Testing

JCW 7-Port 1 PM (Filterable) 0.0413 FALSE 1720 JCW 7-2008 PM Testing

JCW 7-Port 2 PM (Filterable) 0.0478 FALSE

Page 74sampling_run_pollutants1

em ission_rate

em ission_rate_units

em ission_rate_ND

em ission_rate_MDL

em ission_factor

em ission_factor_units

em ission_factor_ND

em ission_factor_MDL

run_pollutant_comment 126.26 pound per hour (lb/hr)

FALSE 0.0719 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 209.4 pound per hour (lb/hr)

FALSE 0.1229 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 174.56 pound per hour (lb/hr)

FALSE 0.0954 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 148.71 pound per hour (lb/hr)

FALSE 0.0864 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 177.56 pound per hour (lb/hr)

FALSE 0.1016 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 119.53 pound per hour (lb/hr)

FALSE 0.0628 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 71.9 pound per hour (lb/hr)

FALSE 0.0376 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 64.66 pound per hour (lb/hr)

FALSE 0.0338 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 85.13 pound per hour (lb/hr)

FALSE 0.0447 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhaust gas 107.27 FALSE 0.0602 FALSE lbs/1000 lbs exhuast gas, 50%air 93.06 pound per hour (lb/hr)

FALSE 0.0406 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhaust gas FALSE FALSE ug/wscm 146.19 pound per hour (lb/hr)

FALSE 0.0469 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas 46.67 pound per hour (lb/hr)

FALSE 0.0253 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 86.33 pound per hour (lb/hr)

FALSE 0.0452 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000 lbs exhuast gas 90.59 pound per hour (lb/hr)

FALSE 0.0505 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas 104.97 pound per hour (lb/hr)

FALSE 0.0582 pound per million British Thermal Unit (lb/MMBtu) FALSE lbs/1000lbs exhuast gas

Page 75sampling_run_pollutants1 run_pollutant_comment lbs/1000lbs exhuast gas lbs/1000lbs exhuast gas lbs/1000lbs exhuast gas lbs/1000lbs exhuast gas lbs/1000lbs exhuast gas lbs/1000lbs exhaust gas lbs/1000lbs exhaust gas lbs/1000lbs exhaust gas lbs/1000lbs exhaust gas lbs/1000 lbs exhuast gas, 50%air lbs/1000 lbs exhaust gas lbs/1000 lbs exhuast gas lbs/1000lbs exhuast gas lbs/1000 lbs exhuast gas lbs/1000lbs exhuast gas lbs/1000lbs exhuast gas

Page 76sampling_run_fuel

facility _id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_ND

fuel_conc_MDL

Page 77sampling_run_fuel fuel_conc_MDL

Page 78