Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Yellowstone Energy LP

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Thursday, January 20, 2011 Page 1 of 30
Yellowstone Energy LP

Facility Information:

Yellowstone Energy LP

2215 N. Frontage Road

Billings MT 59101-7307

Contact: Scott Soddoway

Phone: 2083443570

Fax:

Email: scott.siddoway@rosi-boise.com

Testing Company:

Bison Enineering Inc.

1400 11th Ave

Helena MT 59601

Contact: Steve Fryberger

Phone: 4066331523

Fax: 4068961725

Email: sfryberger@bison-eng.com

Air Permit Number:

OP2650-01

Permitted Source ID/Name:

50931 Yellowstone Energy LP

Permitted Maximum Process Rate:

871 MMBTu/hr

Max. Normal Operation Process Rate:

1036 MMBTu/hr

Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 030-111-0023A FRS #: 110001474164

SCC / Description

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

BLR1 stack 96 0 0 714 780 2 12

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

BLR1 stack Flowrate Method 1 - 4 3 60 0

BLR1 stack % H2O Method 1 - 4 3 60 0

BLR1 stack Carbon Monoxide Method 10 3 60 0

BLR1 stack Formaldehyde Method 0011 3 120 0

BLR1 stack 2,3,7,8-TCDD Method 23 3 480 0

BLR1 stack 1,2,3,7,8-PeCDD Method 23 3 480 0

BLR1 stack 1,2,3,4,7,8-HxCDD Method 23 3 480 0

BLR1 stack 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Thursday, January 20, 2011 Page 2 of 30
Yellowstone Energy LP

BLR1 stack 1,2,3,7,8,9-HxCDD Method 23 3 480 0

BLR1 stack 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

BLR1 stack OCDD Method 23 3 480 0

BLR1 stack 2,3,7,8-TCDF Method 23 3 480 0

BLR1 stack 1,2,3,7,8-PeCDF Method 23 3 480 0

BLR1 stack 2,3,4,7,8-PeCDF Method 23 3 480 0

BLR1 stack 1,2,3,4,7,8-HxCDF Method 23 3 480 0

BLR1 stack 1,2,3,6,7,8-HxCDF Method 23 3 480 0

BLR1 stack 2,3,4,6,7,8-HxCDF Method 23 3 480 0

BLR1 stack 1,2,3,7,8,9-HxCDF Method 23 3 480 0

BLR1 stack 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

BLR1 stack 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

BLR1 stack OCDF Method 23 3 480 0

BLR1 stack Other TCDD Method 23 3 480 0

BLR1 stack Other PeCDD Method 23 3 480 0

BLR1 stack Other HxCDD Method 23 3 480 0

BLR1 stack Other HpCDD Method 23 3 480 0

BLR1 stack Other TCDF Method 23 3 480 0

BLR1 stack Other PeCDF Method 23 3 480 0

BLR1 stack Other HxCDF Method 23 3 480 0

BLR1 stack Other HpCDF Method 23 3 480 0

BLR1 stack Total Dioxins Method 23 3 480 0

BLR1 stack Total Furans Method 23 3 480 0

BLR1 stack 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

BLR1 stack 3,4,4',5-TCB (PCB81) Method 23 3 480 0

BLR1 stack 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

BLR1 stack 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

BLR1 stack 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

BLR1 stack 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

BLR1 stack 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

BLR1 stack Method 23 3 480 0

BLR1 stack 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

BLR1 stack 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

BLR1 stack Method 23 3 480 0

BLR1 stack Other Mono-CBs Method 23 3 480 0

BLR1 stack Other Di-CBs Method 23 3 480 0

BLR1 stack Other Tri-CBs Method 23 3 480 0

BLR1 stack Other Tetra-CBs Method 23 3 480 0

BLR1 stack Other Penta-CBs Method 23 3 480 0

BLR1 stack Other Hexa-CBs Method 23 3 480 0

BLR1 stack Other Hepta-CBs Method 23 3 480 0

BLR1 stack Other Octa-CBs Method 23 3 480 0

BLR1 stack Other Nona-CBs Method 23 3 480 0

BLR1 stack DeCB Method 23 3 480 0

BLR1 stack Total PCBs Method 23 3 480 0

BLR1 stack Total TEQ Method 23 3 480 0

BLR1 stack Naphthalene** Method 23 3 480 0

BLR1 stack 2-Methylnaphthalene Method 23 3 480 0

BLR1 stack Acenaphthylene** Method 23 3 480 0

BLR1 stack Acenaphthene** Method 23 3 480 0

Thursday, January 20, 2011 Page 3 of 30
Yellowstone Energy LP

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

None

BLR1 stack Fluorene** Method 23 3 480 0

BLR1 stack Phenanthrene** Method 23 3 480 0

BLR1 stack Anthracene** Method 23 3 480 0

BLR1 stack Fluoranthene** Method 23 3 480 0

BLR1 stack Pyrene** Method 23 3 480 0

BLR1 stack Benzo(a)Anthracene* Method 23 3 480 0

BLR1 stack Chrysene* Method 23 3 480 0

BLR1 stack Benzo(b)Fluoranthene* Method 23 3 480 0

BLR1 stack Benzo(k)Fluoranthene* Method 23 3 480 0

BLR1 stack Benzo(e)Pyrene Method 23 3 480 0

BLR1 stack Benzo(a)Pyrene* Method 23 3 480 0

BLR1 stack Perylene Method 23 3 480 0

BLR1 stack Indeno(1,2,3-cd)Pyrene* Method 23 3 480 0

BLR1 stack Dibenzo(a,h)Anthracene* Method 23 3 480 0

BLR1 stack Benzo(ghi)Perylene** Method 23 3 480 0

BLR1 stack Total 7*PAH Method 23 3 480 0

BLR1 stack Total 16*/**PAH Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Method 25A 3 60 0 Nonmethane TOC as 

propane

BLR1 stack

BLR1 stack Hydrogen Chloride Method 26 3 180 0

BLR1 stack Hydrogen Fluoride Method 26 3 180 0

Inorganic (Aqueous) 

Condensible Part.

BLR1 stack OTM - 27/28 3 240 0

BLR1 stack Filterable PM2.5 OTM - 27/28 3 240 0

BLR1 stack Total PM2.5 OTM - 27/28 3 240 0

Organic Condensible 

Particulate

BLR1 stack OTM - 27/28 3 240 0

BLR1 stack Arsenic Method 29 3 240 0

BLR1 stack Cobalt Method 29 3 240 0

BLR1 stack Barium Method 29 3 240 0

BLR1 stack Copper Method 29 3 240 0

BLR1 stack Beryllium Method 29 3 240 0

BLR1 stack Manganese Method 29 3 240 0

BLR1 stack Thallium Method 29 3 240 0

BLR1 stack Chromium Method 29 3 240 0

BLR1 stack Silver Method 29 3 240 0

BLR1 stack Zinc Method 29 3 240 0

BLR1 stack Lead Method 29 3 240 0

BLR1 stack Mercury Method 29 3 240 0

BLR1 stack Nickel Method 29 3 240 0

BLR1 stack Selenium Method 29 3 240 0

BLR1 stack Cadmium Method 29 3 240 0

BLR1 stack Antimony Method 29 3 240 0

BLR1 stack Nitrogen oxides (NOx) Method 7E 3 120 0

Thursday, January 20, 2011 Page 4 of 30
Yellowstone Energy LP

Sampling / Stack Data Results Summary

Location BLR1 stack - Method 0011

Average

Run Number 1 2 3

Test Date 5/13/2010 5/14/2010 5/13/2010

Run Start Time 6:40:00 PM 9:00:00 

AM

11:50:00 AM

Run Finish Time 8:30:00 PM 10:50:00 

AM

1:40:00 PM

Net Run Time, minutes 120 120 120

Dry Gas Meter Volume Sampled, dscf 138.933 134.481 128.526 133.980

Moisture Content of Stack Gas, % 7.69 6.89 7.16 7.247

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11 15.34 11 12.447

Oxygen, % 6 4.89 6 5.630

Average Stack Gas Temperature, °F 312.67 313.92 314.25 313.613

Dry Volumetric Flow Rate, dry scfm 230,302.9 227,269.7 220,132.2 225,901.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 406,995.7 399,275.0 388,025.7 398,098.800

Percent Isokinetic of Sampling Rate, % 97.5 95.6 94.4 95.833

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location BLR1 stack - Method 10

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 11:33:00 AM 2:04:00 PM 4:38:00 PM

Run Finish Time 1:33:00 PM 4:04:00 PM 6:38:00 PM

Carbon Dioxide, % 15.11 16.06 16.06 15.743

Oxygen, % 4.8 4.78 4.78 4.787

Dry Volumetric Flow Rate, dry scfm 297933 256452 256452 270,279.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 11.62 8.62 8.62 9.620

Fuel Type Override Override Override

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 5 of 30
Yellowstone Energy LP

Location BLR1 stack - Method 23

Average

Run Number 1 2 3

Test Date 5/11/2010 5/12/2010 5/13/2010

Run Start Time 10:45:00 AM 8:15:00 

AM

8:57:00 AM

Run Finish Time 2:25:00 PM 11:55:00 

AM

12:37:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 192.258 197.817 188.416 192.830

Moisture Content of Stack Gas, % 15.83 14.53 13.76 14.707

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 16.06 14.98 14.94 15.327

Oxygen, % 4.78 5.02 5.19 4.997

Average Stack Gas Temperature, °F 307.92 309.67 310.33 309.307

Dry Volumetric Flow Rate, dry scfm 204,600.9 207,903.7 202,347.2 204,950.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 396,319.4 395,716.2 381,601.8 391,212.467

Percent Isokinetic of Sampling Rate, % 105.4 106.8 104.5 105.567

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location BLR1 stack - Method 25A

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 11:33:00 AM 2:04:00 PM 4:38:00 PM

Run Finish Time 1:33:00 PM 4:04:00 PM 6:38:00 PM

Carbon Dioxide, % 16.06 16.06 16.06 16.060

Oxygen, % 4.78 4.78 4.78 4.780

Dry Volumetric Flow Rate, dry scfm 256452 256452 256452 256,452.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.62 8.62 8.62 8.620

Fuel Type Override Override Override

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 6 of 30
Yellowstone Energy LP

Location BLR1 stack - Method 29

Average

Run Number 1 2 3

Test Date 5/12/2010 5/13/2010 5/13/2010

Run Start Time 4:35:00 PM 9:13:00 

AM

1:48:00 PM

Run Finish Time 8:15:00 PM 12:53:00 

PM

5:28:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 227.780 285.442 265.215 259.479

Moisture Content of Stack Gas, % 7.54 7.31 7.65 7.500

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14.95 15.02 14.84 14.937

Oxygen, % 5.03 5.14 5.26 5.143

Average Stack Gas Temperature, °F 310.00 309.75 313.00 310.917

Dry Volumetric Flow Rate, dry scfm 247,527.7 227,435.8 221,669.0 232,210.833

Actual Wet Volumetric Flue Gas Flow Rate, acfm 391,855.9 399,214.7 391,735.3 394,268.633

Percent Isokinetic of Sampling Rate, % 103.2 101.4 96.7 100.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location BLR1 stack - Method 7E

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 11:33:00 AM 2:04:00 PM 4:38:00 PM

Run Finish Time 1:33:00 PM 4:04:00 PM 6:38:00 PM

Carbon Dioxide, % 16.06 16.06 16.06 16.060

Oxygen, % 4.78 4.78 4.78 4.780

Dry Volumetric Flow Rate, dry scfm 256452 256452 256452 256,452.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.62 8.62 8.62 8.620

Fuel Type Override Override Override

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 7 of 30
Yellowstone Energy LP

Location BLR1 stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 11:50:00 AM 8:10:00 

AM

11:15:00 AM

Run Finish Time 3:30:00 PM 11:50:00 

AM

2:55:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 85.686 88.284 87.975 87.315

Moisture Content of Stack Gas, % 11.61 11.17 12.35 11.710

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 16.06 14.98 15.03 15.357

Oxygen, % 4.78 5.04 4.96 4.927

Average Stack Gas Temperature, °F 309.17 312.00 307.83 309.667

Dry Volumetric Flow Rate, dry scfm 247,597.9 227,732.4 222,781.9 232,704.067

Actual Wet Volumetric Flue Gas Flow Rate, acfm 457,451.7 420,205.3 414,354.5 430,670.500

Percent Isokinetic of Sampling Rate, % 85.0 95.3 97.0 92.433

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 8 of 30
Yellowstone Energy LP

Emissions Summary

Location: BLR1 stack - Method 0011

Compound: Formaldehyde

Average

RunNumber 1 2 3

Mass_mg 0.62 1.2 0.54 0.787

lb/mmBtuO2 1.27E-04 2.36E-04 1.19E-04 0.000

ppm 1.26E-01 2.52E-01 1.19E-01 0.166

ppm@7%O2 1.18E-01 2.19E-01 1.11E-01 0.149

Location: BLR1 stack - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 9.48E-03 1.06E-02 9.12E-03 0.010

ppm 1.09E+01 1.23E+01 1.05E+01 11.233

ppm@7%O2 9.41E+00 1.06E+01 9.05E+00 9.687

Location: BLR1 stack - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000033 0.00000000603 0.00000000655 0.000

ng/dscm 6.06E-04 1.08E-03 1.23E-03 0.001

ng/dscm@7%O2 5.23E-04 9.45E-04 1.09E-03 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000568 0.00000000957 0.00000000459 0.000

ng/dscm 1.04E-03 1.71E-03 8.60E-04 0.001

ng/dscm@7%O2 8.97E-04 1.50E-03 7.61E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000521 0.00000000397 0.00000000698 0.000

ng/dscm 9.57E-04 7.09E-04 1.31E-03 0.001

ng/dscm@7%O2 8.25E-04 6.21E-04 1.16E-03 0.001

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000218 0.00000000291 0.00000000411 0.000

ng/dscm 4.00E-04 5.20E-04 7.70E-04 0.001

ng/dscm@7%O2 3.45E-04 4.55E-04 6.81E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000272 0.00000000205 0.00000000245 0.000

Thursday, January 20, 2011 Page 9 of 30
Yellowstone Energy LP

ng/dscm 5.00E-04 3.66E-04 4.59E-04 0.000

ng/dscm@7%O2 4.31E-04 3.20E-04 4.06E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000231 0.00000000317 0.00000000435 0.000

ng/dscm 4.24E-04 5.66E-04 8.15E-04 0.001

ng/dscm@7%O2 3.66E-04 4.95E-04 7.21E-04 0.001

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000285 0.0000000017 0.00000000229 0.000

ng/dscm 5.24E-04 3.04E-04 4.29E-04 0.000

ng/dscm@7%O2 4.52E-04 2.66E-04 3.80E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000236 0.00000000343 0.00000000488 0.000

ng/dscm 4.34E-04 6.12E-04 9.15E-04 0.001

ng/dscm@7%O2 3.74E-04 5.36E-04 8.10E-04 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000165 0.00000000154 0.00000000308 0.000

ng/dscm 3.03E-04 2.75E-04 5.77E-04 0.000

ng/dscm@7%O2 2.61E-04 2.41E-04 5.11E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000201 0.00000000206 0.00000000267 0.000

ng/dscm 3.69E-04 3.68E-04 5.01E-04 0.000

ng/dscm@7%O2 3.18E-04 3.22E-04 4.43E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000229 0.00000000157 0.00000000181 0.000

ng/dscm 4.21E-04 2.80E-04 3.39E-04 0.000

ng/dscm@7%O2 3.63E-04 2.45E-04 3.00E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.00000000558 0.00000000907 0.00000000805 0.000

ng/dscm 1.03E-03 1.62E-03 1.51E-03 0.001

ng/dscm@7%O2 8.88E-04 1.42E-03 1.34E-03 0.001

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

Thursday, January 20, 2011 Page 10 of 30
Yellowstone Energy LP

RunNumber 1 2 3

Mass_mg 0.0000000789 0.000000163 0 0.000

ng/dscm 1.45E-02 2.91E-02 0.00E+00 0.015

ng/dscm@7%O2 1.25E-02 2.55E-02 0.00E+00 0.013

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000279 0.000000579 0.000000524 0.000

ng/dscm 5.13E-02 1.03E-01 9.82E-02 0.084

ng/dscm@7%O2 4.42E-02 9.02E-02 8.69E-02 0.074

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000267 0.000000052 0.0000000552 0.000

ng/dscm 4.91E-03 9.28E-03 1.03E-02 0.008

ng/dscm@7%O2 4.23E-03 8.12E-03 9.11E-03 0.007

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000148 0.0000000298 0.0000000258 0.000

ng/dscm 2.72E-03 5.32E-03 4.84E-03 0.004

ng/dscm@7%O2 2.35E-03 4.66E-03 4.28E-03 0.004

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.000000615 0.00000119 0.0000011 0.000

ng/dscm 1.13E-01 2.12E-01 2.06E-01 0.177

ng/dscm@7%O2 9.74E-02 1.86E-01 1.82E-01 0.155

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000138 0.0000000195 0.0000000231 0.000

ng/dscm 2.54E-03 3.48E-03 4.33E-03 0.003

ng/dscm@7%O2 2.19E-03 3.05E-03 3.83E-03 0.003

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000251 0.00000000295 0.00000000235 0.000

ng/dscm 4.61E-04 5.27E-04 4.41E-04 0.000

ng/dscm@7%O2 3.98E-04 4.61E-04 3.90E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000349 0.00000000152 0.00000000181 0.000

ng/dscm 6.41E-04 2.71E-04 3.39E-04 0.000

ng/dscm@7%O2 5.53E-04 2.37E-04 3.00E-04 0.000

Thursday, January 20, 2011 Page 11 of 30
Yellowstone Energy LP

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000126 0.00000000134 0.00000000185 0.000

ng/dscm 2.31E-04 2.39E-04 3.47E-04 0.000

ng/dscm@7%O2 1.99E-04 2.09E-04 3.07E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000518 0.0000000012 0.00000000168 0.000

ng/dscm 9.52E-04 2.14E-04 3.15E-04 0.000

ng/dscm@7%O2 8.21E-04 1.87E-04 2.79E-04 0.000

Compound: 2-Methylnaphthalene

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000000388 0.00000000608 0.00000000359 0.000

ng/dscm 7.13E-04 1.09E-03 6.73E-04 0.001

ng/dscm@7%O2 6.15E-04 9.54E-04 5.95E-04 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000054 0.00000000758 0.00000000642 0.000

ng/dscm 9.92E-04 1.35E-03 1.20E-03 0.001

ng/dscm@7%O2 8.55E-04 1.18E-03 1.06E-03 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000000324 0.0000000515 0.0000000758 0.000

ng/dscm 5.95E-03 9.20E-03 1.42E-02 0.010

ng/dscm@7%O2 5.13E-03 8.05E-03 1.26E-02 0.009

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.00000000365 0.00000000371 0.00000000654 0.000

ng/dscm 6.71E-04 6.62E-04 1.23E-03 0.001

ng/dscm@7%O2 5.79E-04 5.79E-04 1.09E-03 0.001

Compound: Acenaphthene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

Thursday, January 20, 2011 Page 12 of 30
Yellowstone Energy LP

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Acenaphthylene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Anthracene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Benzo(a)Anthracene*

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Benzo(a)Pyrene*

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Benzo(b)Fluoranthene*

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Benzo(e)Pyrene

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Benzo(ghi)Perylene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Benzo(k)Fluoranthene*

Average

Thursday, January 20, 2011 Page 13 of 30
Yellowstone Energy LP

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Chrysene*

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: DeCB

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Dibenzo(a,h)Anthracene*

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Fluoranthene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Fluorene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Indeno(1,2,3-cd)Pyrene*

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Naphthalene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Thursday, January 20, 2011 Page 14 of 30
Yellowstone Energy LP

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000002 0.0000000403 0.0000000392 0.000

ng/dscm 3.67E-03 7.20E-03 7.35E-03 0.006

ng/dscm@7%O2 3.16E-03 6.30E-03 6.50E-03 0.005

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000674 0.0000000101 0.00000000888 0.000

ng/dscm 1.24E-03 1.80E-03 1.66E-03 0.002

ng/dscm@7%O2 1.07E-03 1.58E-03 1.47E-03 0.001

Compound: Other Di-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Hepta-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Hexa-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

Thursday, January 20, 2011 Page 15 of 30
Yellowstone Energy LP

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Mono-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Nona-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Octa-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Penta-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDD

Average

Thursday, January 20, 2011 Page 16 of 30
Yellowstone Energy LP

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Tetra-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other Tri-CBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Perylene

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Phenanthrene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Pyrene**

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total 16*/**PAH

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Thursday, January 20, 2011 Page 17 of 30
Yellowstone Energy LP

Compound: Total 7*PAH

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total PCBs

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: BLR1 stack - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 -2.91E-04 -1.45E-05 3.54E-04 0.000

ppm -2.13E-01 -1.06E-02 2.60E-01 0.012

ppm@7%O2 -1.84E-01 -9.14E-03 2.24E-01 0.010

Location: BLR1 stack - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.00022 0.00022 0.00022 0.000

lb/mmBtuO2 2.58E-08 2.07E-08 2.25E-08 0.000

Compound: Arsenic

Average

Thursday, January 20, 2011 Page 18 of 30
Yellowstone Energy LP

RunNumber 1 2 3

Mass_mg 0.0022 0.0022 0.0022 0.002

lb/mmBtuO2 2.58E-07 2.07E-07 2.25E-07 0.000

Compound: Barium

Average

RunNumber 1 2 3

Mass_mg 0.3 0.3 0.3 0.300

lb/mmBtuO2 3.51E-05 2.82E-05 3.06E-05 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00011 0.00011 0.00011 0.000

lb/mmBtuO2 1.29E-08 1.04E-08 1.12E-08 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00098 0.00065 0.00034 0.001

lb/mmBtuO2 1.15E-07 6.12E-08 3.47E-08 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0029 0.0042 0.0031 0.003

lb/mmBtuO2 3.40E-07 3.95E-07 3.16E-07 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.00259 0.0191 0.00085 0.008

lb/mmBtuO2 3.03E-07 1.80E-06 8.68E-08 0.000

Compound: Copper

Average

RunNumber 1 2 3

Mass_mg 0.0062 0.0077 0.0101 0.008

lb/mmBtuO2 7.26E-07 7.25E-07 1.03E-06 0.000

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.00298 0.00156 0.00245 0.002

lb/mmBtuO2 3.49E-07 1.47E-07 2.50E-07 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0162 0.01118 0.01384 0.014

lb/mmBtuO2 1.90E-06 1.05E-06 1.41E-06 0.000

Compound: Mercury

Average

Thursday, January 20, 2011 Page 19 of 30
Yellowstone Energy LP

RunNumber 1 2 3

Mass_mg 0.00035 0.00035 0.0004 0.000

lb/mmBtuO2 4.10E-08 3.29E-08 4.08E-08 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.0687 0.0896 0.1013 0.087

lb/mmBtuO2 8.05E-06 8.43E-06 1.03E-05 0.000

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0055 0.0055 0.0055 0.006

lb/mmBtuO2 6.44E-07 5.18E-07 5.61E-07 0.000

Compound: Silver

Average

RunNumber 1 2 3

Mass_mg 0.00198 0.00018 0.0003 0.001

lb/mmBtuO2 2.32E-07 1.69E-08 3.06E-08 0.000

Compound: Thallium

Average

RunNumber 1 2 3

Mass_mg 0.00011 0.00011 0.00011 0.000

lb/mmBtuO2 1.29E-08 1.04E-08 1.12E-08 0.000

Compound: Zinc

Average

RunNumber 1 2 3

Mass_mg 0.1 0.1 0.1 0.100

lb/mmBtuO2 1.17E-05 9.41E-06 1.02E-05 0.000

Location: BLR1 stack - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 1.38E-01 2.09E-01 2.12E-01 0.186

ppm 9.69E+01 1.47E+02 1.49E+02 130.967

ppm@7%O2 8.36E+01 1.27E+02 1.28E+02 112.867

Location: BLR1 stack - OTM - 27/28

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 30.5 25.5 41.5 32.500

lb/mmBtuO2 9.35E-03 7.71E-03 1.25E-02 0.010

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 14.7 19.8 10.7 15.067

Thursday, January 20, 2011 Page 20 of 30
Yellowstone Energy LP

Process Run Data

lb/mmBtuO2 4.51E-03 5.99E-03 3.23E-03 0.005

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 21.4 21.1 16 19.500

lb/mmBtuO2 6.56E-03 6.38E-03 4.83E-03 0.006

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 66.6 66.4 68.2 67.067

lb/mmBtuO2 2.04E-02 2.01E-02 2.06E-02 0.020

Thursday, January 20, 2011 Page 21 of 30
Yellowstone Energy LP

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 U1 Coke flow 38.84 psig 0

2 U1 Coke flow 36.07 psig 0

3 U1 Coke flow 35.88 psig 0

4 U1 Coke flow 35.52 psig 0

1 U2 Coke flow 38.66 psig 0

2 U2 Coke flow 35.03 psig 0

3 U2 Coke flow 37.85 psig 0

4 U2 Coke flow 35.68 psig 0

1 Coker Gas flow 77.89 pph 0

2 Coker Gas flow 77.49 pph 0

3 Coker Gas flow 76.63 pph 0

4 Coker Gas flow 68.89 pph 0

1 U1 Steam flow 949.90 KPPH 0

2 U1 Steam flow 330.73 KPPH 0

3 U1 Steam flow 312.33 KPPH 0

4 U1 Steam flow 322.88 KPPH 0

1 U2 Steam flow 330.4 KPPH 0

2 U2 Steam flow 325.88 KPPH 0

3 U2 Steam flow 313.48 KPPH 0

4 U2 Steam flow 316.9 KPPH 0

1 Gross MW 66.97 Gross MW 60

2 Gross MW 68.18 Gross MW 60

3 Gross MW 68.63 Gross MW 60

4 Gross MW 69.61 Gross MW 60

1 Net MW 57.4 Net MW 50

2 Net MW 58.69 Net MW 50

3 Net MW 57.87 Net MW 50

4 Net MW 59.53 Net MW 50

Run Name Value UOM Comments

Target

Value

1 BAGHOUSE 0 0

1 DRY LIMESTONE INJECTION 0 0

Thursday, January 20, 2011 Page 22 of 30
Yellowstone Energy LP

Process Lab Run Data

Run Name Value UOM Comments

1 na 0

Thursday, January 20, 2011 Page 23 of 30
Yellowstone Energy LP

Sampling / Stack Data Results Detail

Location BLR1 stack - Method 0011

Average

Run Number 1 2 3

Test Date 5/13/2010 5/14/2010 5/13/2010

Run Start Time 6:40:00 PM 9:00:00 AM 11:50:00 AM

Run Finish Time 8:30:00 PM 10:50:00 AM 1:40:00 PM

Net Traversing Points 12 13 12

Net Run Time, minutes 120 120 120

Nozzle Diameter, inches 0.218 0.218 0.218 0.218

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.04 1.04 1.04 1.040

Barometric Pressure, inches of Mercury 26.99 26.96 26.96 26.970

Average Orifice Meter Differential, inches H2O 5.17 5.20 4.58 4.983

Dry Gas Meter Volume Sampled, cubic feet 145.700 142.895 140.600 143.065

Average Dry Gas Meter Temperature, °F 66.79 73.21 88.04 76.013

Dry Gas Meter Volume Sampled, dscf 138.933 134.481 128.526 133.980

Total Moisture Liquid collected, g 245.8 211.3 210.6 222.567

Volume of Water Vapor, standard cubic feet 11.57 9.95 9.91 10.477

Moisture Content of Stack Gas, % 7.69 6.89 7.16 7.247

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9231 0.9311 0.9284 0.928

Carbon Dioxide, % 11 15.34 11 12.447

Oxygen, % 6 4.89 6 5.630

Carbon Monoxide & Nitrogen, % 83 79.77 83 81.923

Fuel Factor 1.35 1.04 1.35

Dry Molecular Weight, lb/lb-Mole 30.00 30.65 30.00 30.217

Wet Molecular weight, lb/lb-Mole 29.08 29.78 29.14 29.333

Flue Gas Static Pressure, inches of H2O -2 -2 -2 -2.000

Absolute Flue Gas Pressure, inches of Mercury 26.84 26.81 26.81 26.820

Average Stack Gas Temperature, °F 312.67 313.92 314.25 313.613

Average Velocity Head, inches of H2O 3.5670870113

1361

3.506026547

9559

3.238914822

5652

3.437

Average Stack Gas Velocity, feet/second 134.95 132.39 128.66 132.000

Stack Cross-Sectional Area, square feet 50.265 50.265 50.265 50.265

Dry Volumetric Flow Rate, dry scfm 230,302.9 227,269.7 220,132.2 225,901.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 406,995.7 399,275.0 388,025.7 398,098.800

Percent Isokinetic of Sampling Rate, % 97.5 95.6 94.4 95.833

Percent Excess Air, % 37.7 30.2 37.7 35.200

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 96 96 96

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 24 of 30
Yellowstone Energy LP

Location BLR1 stack - Method 10

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 11:33:00 AM 2:04:00 PM 4:38:00 PM

Run Finish Time 1:33:00 PM 4:04:00 PM 6:38:00 PM

Carbon Dioxide, % 15.11 16.06 16.06 15.743

Oxygen, % 4.8 4.78 4.78 4.787

Fuel Factor 1.07 1 1

Dry Volumetric Flow Rate, dry scfm 297933 256452 256452 270,279.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 11.62 8.62 8.62 9.620

Analyzer Make Thermo

Analyzer Model 48i-HL

Analyzer Serial Number 734025183 734,025,183

.000

Operating Range 10000 0 0 3,333.333

Operating Units ppm

No. Readings/Avg. 1 0 0 0.333

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID Zero Air Zero Air Zero Air

Calibration Pre Zero Cylinder Instrument Response -0.23 -0.08 -1.1 -0.470

Calibration Pre Zero Cylinder Bias 0.54 0.84 -1.2 0.060

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM048635-

25

ALM048635

-25

ALM048635-

25

Calibration Pre High Cylinder Instrument Response 25.33 24.4 24.72 24.817

Calibration Pre High Cylinder Bias 0.26 -1.6 -0.96 -0.767

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Air Zero Air Zero Air

Calibration Post Zero Cylinder Instrument Response -0.08 -1.1 1.85 0.223

Calibration Post Zero Cylinder Bias 0.84 -1.2 4.7 1.447

Calibration Post Zero Cylinder Drift 0.3 2.04 5.9 2.747

Calibration Post High Cylinder ID ALM048635-

25

ALM048635

-25

ALM048635-

25

Calibration Post High Cylinder Instrument Response 24.4 24.72 24.56 24.560

Calibration Post High Cylinder Bias -1.6 -0.96 -1.28 -1.280

Calibration Post High Cylinder Drift 1.86 0.64 0.32 0.940

Cavg 10.79 11.76 10.59 11.047

Cavg Units ppmvd ppmvd ppmvd

Cgas 10.9363 12.2763 10.5244 11.246

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, January 20, 2011 Page 25 of 30
Yellowstone Energy LP

Location BLR1 stack - Method 23

Average

Run Number 1 2 3

Test Date 5/11/2010 5/12/2010 5/13/2010

Run Start Time 10:45:00 AM 8:15:00 AM 8:57:00 AM

Run Finish Time 2:25:00 PM 11:55:00 AM 12:37:00 PM

Net Traversing Points 13 12 13

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.185 0.185 0.185 0.185

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.952 0.952 0.952 0.952

Barometric Pressure, inches of Mercury 26.84 26.96 26.99 26.930

Average Orifice Meter Differential, inches H2O 2.16 2.30 2.07 2.177

Dry Gas Meter Volume Sampled, cubic feet 225.320 220.070 217.605 220.998

Average Dry Gas Meter Temperature, °F 71.58 47.04 66.63 61.750

Dry Gas Meter Volume Sampled, dscf 192.258 197.817 188.416 192.830

Total Moisture Liquid collected, g 768.4 714.3 638.8 707.167

Volume of Water Vapor, standard cubic feet 36.17 33.62 30.07 33.287

Moisture Content of Stack Gas, % 15.83 14.53 13.76 14.707

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8417 0.8547 0.8624 0.853

Carbon Dioxide, % 16.06 14.98 14.94 15.327

Oxygen, % 4.78 5.02 5.19 4.997

Carbon Monoxide & Nitrogen, % 79.16 80 79.87 79.677

Fuel Factor 1.00 1.06 1.05

Dry Molecular Weight, lb/lb-Mole 30.76 30.60 30.60 30.653

Wet Molecular weight, lb/lb-Mole 28.74 28.77 28.87 28.793

Flue Gas Static Pressure, inches of H2O -2 -2 -2 -2.000

Absolute Flue Gas Pressure, inches of Mercury 26.69 26.81 26.84 26.780

Average Stack Gas Temperature, °F 307.92 309.67 310.33 309.307

Average Velocity Head, inches of H2O 3.3450406968

4975

3.345418046

84802

3.122675763

1832

3.271

Average Stack Gas Velocity, feet/second 131.41 131.21 126.53 129.717

Stack Cross-Sectional Area, square feet 50.265 50.265 50.265 50.265

Dry Volumetric Flow Rate, dry scfm 204,600.9 207,903.7 202,347.2 204,950.600

Actual Wet Volumetric Flue Gas Flow Rate, acfm 396,319.4 395,716.2 381,601.8 391,212.467

Percent Isokinetic of Sampling Rate, % 105.4 106.8 104.5 105.567

Percent Excess Air, % 29.7 31.2 32.7 31.200

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 96 96 96

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 26 of 30
Yellowstone Energy LP

Location BLR1 stack - Method 25A

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 11:33:00 AM 2:04:00 PM 4:38:00 PM

Run Finish Time 1:33:00 PM 4:04:00 PM 6:38:00 PM

Carbon Dioxide, % 16.06 16.06 16.06 16.060

Oxygen, % 4.78 4.78 4.78 4.780

Fuel Factor 1 1 1

Dry Volumetric Flow Rate, dry scfm 256452 256452 256452 256,452.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.62 8.62 8.62 8.620

Analyzer Make Thermo

Analyzer Model 51 51.000

Analyzer Serial Number N/A

Operating Range 10000 1000 0 3,666.667

Operating Units ppm ppm

No. Readings/Avg. 1 120 0 40.333

Calibration Set 3 3 3 3.000

Calibration Pre Zero Cylinder ID Zero Air Zero Air Zero Air

Calibration Pre Zero Cylinder Instrument Response 0.33 0.47 -0.13 0.223

Calibration Pre Zero Cylinder Bias 0.13 0.27 -0.33 0.023

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM002064-

25

ALM002064

-25

ALM002064-

25

Calibration Pre High Cylinder Instrument Response 25 27.1 25.08 25.727

Calibration Pre High Cylinder Bias 0.1 2.2 0.18 0.827

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Air Zero Air Zero Air

Calibration Post Zero Cylinder Instrument Response 0.47 -0.13 0.05 0.130

Calibration Post Zero Cylinder Bias 0.27 -0.33 -0.15 -0.070

Calibration Post Zero Cylinder Drift 0.14 0.6 0.18 0.307

Calibration Post High Cylinder ID ALM002064-

25

ALM002064

-25

ALM002064-

25

Calibration Post High Cylinder Instrument Response 27.1 25.08 25.41 25.863

Calibration Post High Cylinder Bias 2.2 0.18 0.51 0.963

Calibration Post High Cylinder Drift 2.1 2.02 0.33 1.483

Cavg 0.2 0.16 0.2 0.187

Cavg Units ppmvw ppmvw ppmvw

Cgas -0.2133 -0.0106 0.2597 0.012

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw -

0.1949317738

79142

-

9.645061728

39504E-03

0.237294838

837255

0.011

Cgasw Units ppmvw ppmvw ppmvw

Thursday, January 20, 2011 Page 27 of 30
Yellowstone Energy LP

Location BLR1 stack - Method 29

Average

Run Number 1 2 3

Test Date 5/12/2010 5/13/2010 5/13/2010

Run Start Time 4:35:00 PM 9:13:00 AM 1:48:00 PM

Run Finish Time 8:15:00 PM 12:53:00 PM 5:28:00 PM

Net Traversing Points 13 13 13

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.185 0.218 0.218 0.207

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.04 1.04 1.04 1.040

Barometric Pressure, inches of Mercury 29.96 26.96 26.99 27.970

Average Orifice Meter Differential, inches H2O 2.73 5.60 4.88 4.403

Dry Gas Meter Volume Sampled, cubic feet 215.230 299.850 284.580 266.553

Average Dry Gas Meter Temperature, °F 63.04 67.71 78.58 69.777

Dry Gas Meter Volume Sampled, dscf 227.780 285.442 265.215 259.479

Total Moisture Liquid collected, g 394.8 478 466.6 446.467

Volume of Water Vapor, standard cubic feet 18.58 22.50 21.96 21.013

Moisture Content of Stack Gas, % 7.54 7.31 7.65 7.500

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9246 0.9269 0.9235 0.925

Carbon Dioxide, % 14.95 15.02 14.84 14.937

Oxygen, % 5.03 5.14 5.26 5.143

Carbon Monoxide & Nitrogen, % 80.02 79.84 79.9 79.920

Fuel Factor 1.06 1.05 1.05

Dry Molecular Weight, lb/lb-Mole 30.59 30.61 30.58 30.593

Wet Molecular weight, lb/lb-Mole 29.64 29.69 29.62 29.650

Flue Gas Static Pressure, inches of H2O -2 -2 -2 -2.000

Absolute Flue Gas Pressure, inches of Mercury 29.81 26.81 26.84 27.820

Average Stack Gas Temperature, °F 310.00 309.75 313.00 310.917

Average Velocity Head, inches of H2O 3.7563797377

6615

3.513819816

74627

3.364842106

78673

3.545

Average Stack Gas Velocity, feet/second 129.93 132.37 129.89 130.730

Stack Cross-Sectional Area, square feet 50.265 50.265 50.265 50.265

Dry Volumetric Flow Rate, dry scfm 247,527.7 227,435.8 221,669.0 232,210.833

Actual Wet Volumetric Flue Gas Flow Rate, acfm 391,855.9 399,214.7 391,735.3 394,268.633

Percent Isokinetic of Sampling Rate, % 103.2 101.4 96.7 100.433

Percent Excess Air, % 31.3 32.3 33.2 32.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 96 96 96

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 28 of 30
Yellowstone Energy LP

Location BLR1 stack - Method 7E

Average

Run Number 1 2 3

Test Date 5/11/2010 5/11/2010 5/11/2010

Run Start Time 11:33:00 AM 2:04:00 PM 4:38:00 PM

Run Finish Time 1:33:00 PM 4:04:00 PM 6:38:00 PM

Carbon Dioxide, % 16.06 16.06 16.06 16.060

Oxygen, % 4.78 4.78 4.78 4.780

Fuel Factor 1 1 1

Dry Volumetric Flow Rate, dry scfm 256452 256452 256452 256,452.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Moisture, % 8.62 8.62 8.62 8.620

Analyzer Make Thermo

Analyzer Model 42i-HL

Analyzer Serial Number 29825194 29,825,194.

000

Operating Range 10000 0 0 3,333.333

Operating Units ppm

No. Readings/Avg. 1 0 0 0.333

Calibration Set 2 2 2 2.000

Calibration Pre Zero Cylinder ID Zero Air Zero Air Zero Air

Calibration Pre Zero Cylinder Instrument Response 2.6 0.83 0.84 1.423

Calibration Pre Zero Cylinder Bias 0.75 -0.14 -0.13 0.160

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID ALM048635-

100

ALM048635

-100

ALM048635-

100

Calibration Pre High Cylinder Instrument Response 101.38 99.32 99.05 99.917

Calibration Pre High Cylinder Bias 0.99 -0.04 -0.18 0.257

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID Zero Air Zero Air Zero Air

Calibration Post Zero Cylinder Instrument Response 0.83 0.84 0.84 0.837

Calibration Post Zero Cylinder Bias -0.14 -0.13 -0.13 -0.133

Calibration Post Zero Cylinder Drift 0.89 0.01 0 0.300

Calibration Post High Cylinder ID ALM048635-

100

ALM048635

-100

ALM048635-

100

Calibration Post High Cylinder Instrument Response 99.32 99.05 99.73 99.367

Calibration Post High Cylinder Bias -0.04 -0.18 0.16 -0.020

Calibration Post High Cylinder Drift 1.03 0.14 0.34 0.503

Cavg 97.27 145.28 147.87 130.140

Cavg Units ppmvd ppmvd ppmvd

Cgas 96.8774 146.8683 149.1933 130.980

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Override Override Override

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Cgasw 0 0 0 0.000

Cgasw Units

Thursday, January 20, 2011 Page 29 of 30
Yellowstone Energy LP

Location BLR1 stack - OTM - 27/28

Average

Run Number 1 2 3

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 11:50:00 AM 8:10:00 AM 11:15:00 AM

Run Finish Time 3:30:00 PM 11:50:00 AM 2:55:00 PM

Net Traversing Points 13 13 13

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.125 0.125 0.125 0.125

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.04 1.04 1.04 1.040

Barometric Pressure, inches of Mercury 26.84 26.84 26.84 26.840

Average Orifice Meter Differential, inches H2O 0.46 0.44 0.49 0.463

Dry Gas Meter Volume Sampled, cubic feet 92.150 91.390 91.675 91.738

Average Dry Gas Meter Temperature, °F 70.42 50.54 54.00 58.320

Dry Gas Meter Volume Sampled, dscf 85.686 88.284 87.975 87.315

Total Moisture Liquid collected, g 239.3 235.8 263.4 246.167

Volume of Water Vapor, standard cubic feet 11.26 11.10 12.40 11.587

Moisture Content of Stack Gas, % 11.61 11.17 12.35 11.710

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8839 0.8883 0.8765 0.883

Carbon Dioxide, % 16.06 14.98 15.03 15.357

Oxygen, % 4.78 5.04 4.96 4.927

Carbon Monoxide & Nitrogen, % 79.16 79.98 80.01 79.717

Fuel Factor 1.00 1.06 1.06

Dry Molecular Weight, lb/lb-Mole 30.76 30.60 30.60 30.653

Wet Molecular weight, lb/lb-Mole 29.28 29.19 29.04 29.170

Flue Gas Static Pressure, inches of H2O -2 -2 -2 -2.000

Absolute Flue Gas Pressure, inches of Mercury 26.69 26.69 26.69 26.690

Average Stack Gas Temperature, °F 309.17 312.00 307.83 309.667

Average Velocity Head, inches of H2O 4.5329323898

4547

3.798915925

27943

3.694624323

88161

4.009

Average Stack Gas Velocity, feet/second 151.68 139.33 137.39 142.800

Stack Cross-Sectional Area, square feet 50.265 50.265 50.265 50.265

Dry Volumetric Flow Rate, dry scfm 247,597.9 227,732.4 222,781.9 232,704.067

Actual Wet Volumetric Flue Gas Flow Rate, acfm 457,451.7 420,205.3 414,354.5 430,670.500

Percent Isokinetic of Sampling Rate, % 85.0 95.3 97.0 92.433

Percent Excess Air, % 29.7 31.4 30.7 30.600

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 96 96 96

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Thursday, January 20, 2011 Page 30 of 30