### Name: Kevin Holbrooks

Title: Director, Environmental Compliance Company: St. Johns River Power Park Sign Date: Name: Carl Vineyard Title: Utility MACT Program Director Company: Grace Consulting, Inc. Sign Date: 6/25/2010 Permitted Facility Representative / Date Testing Company Representative / Date 

## St. Johns River Power Park, Unit 2

Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Friday, February 04, 2011 Page 1 of 13

### St. Johns River Power Park, Unit 2

Facility Information:

St. Johns River Power Park

11201 New Berlin Road

Jacksonville FL 32226
Contact: Kevin Holbrooks
Phone: 904-665-4540
Fax: 904-665-4530
Email: holbke@jea.com Testing Company: Grace Consulting, Inc.

510 Dickson Street

Wellington OH 44090
Contact: Carl Vineyard
Phone: 440-647-6672
Fax: 440-467-6673
Email: carlvineyard@aol.com

Air Permit Number:
FL0037869 Permitted Source ID/Name:
Unit 2 SJRPP
Permitted Maximum Process Rate:
660 MW Max. Normal Operation Process Rate:
660 MW Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: SJRPP Unit 2 is a pulverized coal boiler rated at 660MW with a SCR, Electrostatic Precipitator and Scrubber

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 1203100001 FRS #: 110000362134

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous Coal - Pulverized Coal: Dry Bottom (Bituminous Coal)

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
Stack Unit 2 471.44 2350 600 4 0 24 0 0

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 120 0 Stack Unit 2 Total organic compounds

(TOC) as Propane Method 25A 3 120 0 Stack Unit 2

O2 Method 3A O2 3 120 0 Stack Unit 2 Co2 Method 3A CO2 3 120 0 Stack Unit 2 Nitrogen oxides (NOx) Method 7E 3 120 0 Stack Unit 2



### Friday, February 04, 2011 Page 2 of 13

### St. Johns River Power Park, Unit 2

The following describes any modifications and/or deviations to the applicable test methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. There were no modifications to the testing methods.



### Friday, February 04, 2011 Page 3 of 13

### St. Johns River Power Park, Unit 2

Sampling / Stack Data Results Summary



### Location Stack Unit 2 - Method 10 Average
Run Number 1 2 3

Test Date 4/7/2010 4/7/2010 4/7/2010
Run Start Time 6:50:00 AM 9:25:00 AM 11:55:00 AM

Run Finish Time 9:00:00 AM 11:33:00 AM 2:05:00 PM

Carbon Dioxide, % 12.6 12.8 12.8 12.733 Oxygen, % 6.7 6.6 6.6 6.633 Dry Volumetric Flow Rate, dry scfm 1861147 1858073 1843269 1,854,163.00 0 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.51 12.25 14.2 13.320 Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000



### Location Stack Unit 2 - Method 25A Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Friday, February 04, 2011 Page 4 of 13

### St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 3A CO2 Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Location Stack Unit 2 - Method 3A O2 Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Friday, February 04, 2011 Page 5 of 13

### St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 7E Average
Run Number

Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type

Fw

Fc



### Friday, February 04, 2011 Page 6 of 13

### St. Johns River Power Park, Unit 2

Emissions Summary

Process Run Data 

### Location: Stack Unit 2 - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 lb/mmBtuO2 6.72E-02 7.97E-02 1.41E-01 0.096
ppm 6.42E+01 7.67E+01 1.36E+02 92.300 ppm@7%O2 6.28E+01 7.46E+01 1.32E+02 89.800



### Location: Stack Unit 2 - Method 25A Compound: Total organic compounds (TOC) as Average Run 1 2 3 lb/mmBtuO2 7.91E-04 9.79E-04 1.51E-03 0.001
ppm 4.80E-01 5.98E-01 9.21E-01 0.666 ppm@7%O2 4.70E-01 5.81E-01 8.95E-01 0.649



### Location: Stack Unit 2 - Method 7E Compound: Nitrogen oxides (NOx) Average Run 1 2 3 lb/mmBtuO2 6.10E-02 7.97E-02 8.57E-02 0.075
ppm 3.55E+01 4.67E+01 5.02E+01 44.133 ppm@7%O2 3.48E+01 4.54E+01 4.88E+01 43.000



### Friday, February 04, 2011 Page 7 of 13

### St. Johns River Power Park, Unit 2

Process Run Data

APCD Run Data

Process Lab Run Data 

### Run Name Value UOM Comments Target Value
1 Heat Input 5970 mmBTU 5800



### 2 Heat Input 6019 mmBTU 5800

3 Heat Input 6025 mmBTU 5800

1 Steam Flow 4.67 Mlb/hr 4.5



### 2 Steam Flow 4.74 Mlb/hr 4.5

3 Steam Flow 4.74 Mlb/hr 4.5

1 Gross MW 543 MW 650



### 2 Gross MW 670 MW 650

3 Gross MW 630 MW 650



### Run Name Value UOM Comments Target Value
1 SCR (SELECTIVE CATALYTIC REDUCTION) 814 lb/hr 775



### 2 SCR (SELECTIVE CATALYTIC REDUCTION) 819 lb/hr 775

3 SCR (SELECTIVE CATALYTIC REDUCTION) 796 lb/hr 775



### 1 DUAL ALKALI SCRUBBING 112 Kgpm 108

2 DUAL ALKALI SCRUBBING 113 Kgpm 108

3 DUAL ALKALI SCRUBBING 112 Kgpm 108



### 1 ELECTROSTATIC PRECIPITATOR

2 ELECTROSTATIC PRECIPITATOR

3 ELECTROSTATIC PRECIPITATOR



### 1 OVERFIRE AIR

2 OVERFIRE AIR

3 OVERFIRE AIR



### Friday, February 04, 2011 Page 8 of 13

### St. Johns River Power Park, Unit 2

Sampling / Stack Data Results Detail



### Location Stack Unit 2 - Method 10 Average Run Number 1 2 3 Test Date 4/7/2010 4/7/2010 4/7/2010 Run Start Time 6:50:00 AM 9:25:00 AM 11:55:00 AM Run Finish Time 9:00:00 AM 11:33:00 AM 2:05:00 PM Carbon Dioxide, % 12.6 12.8 12.8 12.733 Oxygen, % 6.7 6.6 6.6 6.633 Fuel Factor 1.13 1.12 1.12 Dry Volumetric Flow Rate, dry scfm 1861147 1858073 1843269 1,854,163.0 00 F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000 Moisture, % 13.51 12.25 14.2 13.320 Analyzer Make Horiba Horiba Horiba Analyzer Model VIA-510 VIA-510 VIA-510 Analyzer Serial Number 570124044 570124044 570124044 570,124,044 .000 Operating Range 497 497 497 497.000 Operating Units ppm ppm ppm No. Readings/Avg. 120 120 120 120.000 Calibration Set 1 1 1 1.000 Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Pre Zero Cylinder Instrument Response 1.15 0.03 2.98 1.387 Calibration Pre Zero Cylinder Bias 0.22 0 0.59 0.270 Calibration Pre Zero Cylinder Drift 0 0 0 0.000 Calibration Pre High Cylinder ID EB0004477 EB0004477 EB0004477 Calibration Pre High Cylinder Instrument Response 233.39 231.12 230.17 231.560 Calibration Pre High Cylinder Bias 0.22 -0.24 -0.43 -0.150 Calibration Pre High Cylinder Drift 0 0 0 0.000 Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770 Calibration Post Zero Cylinder Instrument Response 0.03 2.98 2.28 1.763 Calibration Post Zero Cylinder Bias 0 0.59 0.45 0.347 Calibration Post Zero Cylinder Drift 0.22 0.59 0.14 0.317 Calibration Post High Cylinder ID EB0004477 EB0004477 EB0004477 Calibration Post High Cylinder Instrument Response 231.12 230.17 235.72 232.337 Calibration Post High Cylinder Bias -0.24 -0.43 0.69 0.007 Calibration Post High Cylinder Drift 0.46 0.19 1.12 0.590 Cavg 65.3 77.9 138.93 94.043 Cavg Units ppmvd ppmvd ppmvd Cgas 64.2449 76.6817 136.1136 92.347 Cgas Units ppmvd ppmvd ppmvd Fuel Type Coal - Bituminous Coal -

Bituminous Coal -

Bituminous Fw 10640 10640 10640 10,640.000 Fc 1800 1800 1800 1,800.000 Cgasw 0 0 0 0.000 Cgasw Units



### Friday, February 04, 2011 Page 9 of 13

### St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 25A Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 04, 2011 Page 10 of 13

### St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 3A CO2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 04, 2011 Page 11 of 13

### St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 3A O2 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 04, 2011 Page 12 of 13

### St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 7E Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 04, 2011 Page 13 of 13