Revision 4.8, 10/21/13 

Air Pollution Control Operating Permit 

Operating Permit Renewal 

Permit Activity Number: BOP120002 Program Interest Number: 65498

Mailing Address Plant Location 

STEVEN DICARLO 

PLANT MGR 

CHAMBERS COGENERATION LP 

CARNEYS POINT GENERATING PLANT 

500 SHELL RD 

Carneys Point, NJ 08069-2926 

CARNEYS POINT GENERATING PLANT 

500 Shell Rd 

Carneys Point Twp 

Salem County 

Initial Operating Permit Approval Date: March 28, 2003 

Operating Permit Renewal Approval Date: TBD 

Operating Permit Renewal Expiration Date: March 27, 2018

This operating permit renewal is approved and issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 

26:2C-9.2). The facility shall be operated in accordance with the requirements of this permit. 

This operating permit renewal hereby supersedes any previous Air Pollution Control Operating Permit and any 

general operating permits issued to the facility by the Department, and any significant modification, minor 

modification, seven-day notice change, or administrative amendment to such permit. 

This operating permit includes a permit shield, pursuant to the provisions of N.J.A.C. 7:27-22.17. This operating 

permit does not include compliance schedules as part of the approved compliance plan. 

This operating permit renewal also includes the following significant modifications: 

The facility designated the auxiliary boiler as a limited use boiler pursuant to MACT Subpart DDDDD, and 

requested a limitation of 876 operating hours per 12-month rolling period. 

The permittee shall submit to the Department and to the EPA a periodic compliance certification, in accordance with 

N.J.A.C. 7:27-22.19. The certification shall be submitted electronically through the NJDEP online web portal – 

Periodic Compliance Certification service, and shall be certified pursuant to N.J.A.C. 7:27-1.39 by the responsible 

official. Access to DEP Online shall be obtained by following the instructions at: http://www.state.nj.us/dep/online/. 

The certification should be printed for submission to EPA. The schedule for compliance certifications set forth in the 

compliance plan in this operating permit. The annual compliance certification reporting period will cover the 

calendar year ending December 31. The annual compliance certification is due to the Department and the EPA 

within 60 days after the end of each calendar year during which this permit was in effect. 

The annual compliance certification report may also be considered as your six month deviation report for the period 

from July 1 through December 31 which is due by January 30 of each year, as required by paragraph 13 in Section 

E, General Provisions and Authorities, of this permit, if the annual compliance certification is submitted by January 

30. 

 CHRIS CHRISTIE DEPARTMENT of ENVIRONMENTAL PROTECTION BOB MARTIN 

 Governor Commissioner

Division of Air Quality

 KIM GUADAGNO Bureau of Air Permits 

 Lt. Governor 401 E. State Street, 2nd floor, P.O. Box 420, Mail Code 401-02 

Trenton, NJ 08625-0420 
Revision 4.8, 10/21/13 

New Jersey Department of Environmental Protection United States Environmental Protection Agency, Region II 

Air & Environmental Quality Enforcement Air Compliance Branch 

401 East State Street, P. O. Box 422 290 Broadway 

Trenton, New Jersey 08625-0422 New York, New York 10007-1866 

 

New Jersey Department of Environmental Protection 

Air and Environmental Quality Compliance & Enforcement 

Southern Regional Enforcement Office 

2 Riverside Drive 

Camden, New Jersey 08103 

Your facility’s current approved operating permit and any previous versions (e.g. superseded, expired, or 

terminated) are now available for download in the PDF format at: http://www.nj.gov/dep/aqpp/. After accessing the 

website, click on “Approved Operating Permits” listed under “Reports” and then type in the Program Interested (PI) 

Number as instructed on the screen. A RADIUS file for your permit, containing Facility Specific Requirements 

(Compliance Plan), Inventories, and Compliance Schedules (if needed), can be obtained by contacting your permit 

writer. Upon importing this information into your personal computer with RADIUS software, you will have up-todate information in RADIUS format. RADIUS software, instructions, and help are available at the Department's 

website at www.state.nj.us/dep/aqpp. We also have an Operating Permit Help Line available from 9:00 AM to 4:00 

PM daily, where you may speak to someone about any questions you may have. The Operating Permit Help Line 

number is 609-633-8248. 

The permittee is responsible for submitting a timely and administratively complete operating permit renewal 

application. The Operating Permit Renewal Application consists of a RADIUS application and the Application 

Attachment available in Portable Document Format (PDF) and MS Word format at the Department’s website 

http://www.nj.gov/dep/aqpp/applying.html (check Attachment to the RADIUS Operating Permit Renewal 

Application). Both the RADIUS application and the Application Attachment, along with any other supporting 

documents (saved on a CD) must be submitted with a cover letter (paper copy). The application is considered timely 

if it is received at least 12 months before the expiration date of the operating permit. To be deemed administratively 

complete, an application for renewal of the operating permit shall include all of the information required by the 

application form for the renewal and the information required pursuant to N.J.A.C. 7:27-22.30(d). However, 

consistent with N.J.A.C. 7:27-22.30(c), the permittee is encouraged to submit the renewal application at least 15 

months prior to expiration of the operating permit, so that the Department can notify the applicant of any 

deficiencies in the application. This will allow the permittee to correct any deficiencies, and to better ensure that the 

application is administratively complete by the renewal deadline. Only applications which are timely and 

administratively complete will be eligible for coverage by an application shield. 

Permittees that are subject to Compliance Assurance Monitoring (CAM), pursuant to 40 CFR 64, shall develop a 

CAM Plan for modified equipment as well as existing sources. Details of the rule and guidance on how to prepare a 

plan can be found at EPA’s website: www.epa.gov/ttn/emc/cam.html. In addition, CAM Plans must be included as 

part of the permit renewal application. Permittees that do not submit a CAM Plan may have their modification 

applications denied, pursuant to N.J.A.C. 7:27-22.3. 

If, in your judgment, the Department is imposing any unreasonable condition of approval, you may contest the 

Department’s decision and request an adjudicatory hearing pursuant to N.J.S.A. 52:14b-1 et seq. and N.J.A.C. 7:27-

22.32(a). All requests for an adjudicatory hearing must be received in writing by the Department within 20 calendar 

days of the date you receive this letter. The request must contain the information specified at in N.J.A.C. 7:27-1.32 

and the information on the enclosed Administrative Hearing Request Checklist and Tracking Form. 
Revision 4.8, 10/21/13 

If you have any questions regarding this permit approval, please call your permit writer, Shafi Ahmed, at (609) 633-

2971. 

Approved by: 

 ______________________ 

David Owen 

Bureau of Air Permits 

Enclosure 

CC: S. Riva, USEPA Region II 
Revision 4.8, 10/21/13 

Administrative Hearing Request Checklist and Tracking Form 

I. Document Being Appealed 

Name of the Facility 

Program Interest 

(PI) Number

Permit Activity 

Number

Issuance 

Date 

CARNEYS POINT GENERATING PLANT 65498 BOP120002

II. Contact Information 

Name of Person Requesting Hearing Name of Attorney (if applicable)

Address: Address:

Telephone: Telephone:

III. Please include the following information as part of your request: 

A. The date the permittee received the permit decision, 

B. One printed and two PDF (or scanned) copies of the document being appealed saved on 

two CDs – for submitting to address 1 below; 

A PDF (or scanned) copy of all documents being submitted to the Office of Legal Affairs 

saved on a CD – for submitting to address 2 below;

C. The legal and factual questions you are appealing; 

D. A statement as to whether or not you raised each legal and factual issues during the 

permit application process; 

E. Suggested revised or alternative permit conditions; 

F. An estimate of the time required for the hearing; 

G. A request, if necessary, for a barrier-free hearing location for physically disabled persons; 

H. A clear indication of any willingness to negotiate a settlement with the Department prior to 

the Departments processing of your hearing request to the Office of Administrative Law; 

Mail this form, completed, signed and dated with all of the information listed above, including attachment, 

to: 

1. New Jersey Department of Environmental Protection 

Office of Legal Affairs 

Attention: Adjudicatory Hearing Requests 

401 E. State Street, P.O. Box 402 

Trenton, New Jersey 08625-0402 

2. Mr. Bachir Bouzid 

Air Quality Permitting Program 

New Jersey Department of Environmental Protection 

 401 E. State Street, 2nd Floor, P.O. Box 420, Mail Code 401-02 

Trenton, New Jersey 08625-0420 

Phone: (609) 633-2829 

Signature Date
Revision 4.8, 10/21/13 

Administrative Hearing Request Checklist and Tracking Form 

IV. If you are not the applicant but rather an interested person claiming to be aggrieved by the 

permit decision, please include the following information: 

1. The date you or your agent received notice of the permit decision (include a copy of that 

permit decision with your hearing request); 

2. Evidence that a copy of the request has been delivered to the applicant for the permit 

which is the subject of the permit decision; 

3. A detailed statement of which findings of fact and/or conclusion of law you are 

challenging; 

4. A description of your participation in any public hearings held in connection with the 

permit application and copies of any written comments you submitted; 

5. Whether you claim a statutory or constitutional right to a hearing, and, if you claim such a 

right, a reference to the applicable statute or explanation of how your property interests 

are affected by the permit decision; 

6. If the appeal request concerns a CAFRA permit decision, evidence that a copy of the 

request has been delivered to the clerks of the county and the municipality in which the 

project which is the subject of the permit decision is located; 

7. Suggested revised or alternative permit conditions; 

8. An estimate of the time required for the hearing; 

9. A request, if necessary, for a barrier-free hearing location for physically disable persons; 

10. A clear indication of any willingness to negotiate a settlement with the Department prior to 

the Department’s transmittal of the hearing request to the Office of Administrative Law; 

Mail this form, completed, signed and dated with all of the information listed above, including attachment, 

to: 

1. New Jersey Department of Environmental Protection 

Office of Legal Affairs 

Attention: Adjudicatory Hearing Requests 

401 East State Street, P.O. Box 402 

Trenton, New Jersey 08625-0402 

 

2. Mr. Bachir Bouzid 

Air Quality Permitting Program 

New Jersey Department of Environmental Protection 

 401 E. State Street, 2nd Floor, P.O. Box 420, Mail Code 401-02 

Trenton, New Jersey 08625-0420 

Phone: (609) 633-2829 

Signature Date
Revision 4.8, 10/21/13 

 

Facility Name: CARNEYS POINT GENERATING PLANT 

Facility ID No.: 65498 

Activity ID No.: BOP120002 

TABLE OF CONTENTS 

Section A 

REASON FOR PERMIT 

Section B 

DEFINITIONS 

Section C 

POLLUTANT EMISSIONS SUMMARY 

Section D 

POLLUTION PREVENTION REPORTING 

Section E 

GENERAL PROVISIONS AND AUTHORITIES 

Section F 

STATE-ONLY APPLICABLE REQUIREMENTS 

Section G 

COMPLIANCE PLAN AND INVENTORIES

(ATTACHMENTS TO THE FACILITY SPECIFIC REQUIREMENTS) 
Revision 4.8, 10/21/13 

Section A 

Facility Name: CARNEYS POINT GENERATING PLANT 

Program Interest Number: 65498 

Permit Activity Number: BOP120002 

REASON FOR PERMIT 

The reason for issuance of this permit is to comply with the air pollution control permit provisions of Title V of the 

federal Clean Air Act, federal rules promulgated at 40 CFR 70, and state regulations promulgated at N.J.A.C. 7:27-

22, which require the state to issue operating permits to major facilities. This is the renewal of the operating permit 

for the facility listed on the cover page. 

The New Jersey Department of Environmental Protection (Department) issues this operating permit authorizing the 

facility to operate equipment and air pollution control devices. In the operating permit renewal application, the 

facility represented that it meets all applicable requirements of the federal Clean Air Act and the New Jersey Air 

Pollution Control Act codified at N.J.S.A. 26:2C. Based on an evaluation of the data contained in the facility’s 

renewal application, the Department has approved this operating permit. 

This operating permit renewal also includes the following significant modifications: 

The facility designated the auxiliary boiler as a limited use boiler pursuant to MACT Subpart DDDDD, and 

requested a limitation of 876 operating hours per 12-month rolling period. 

This permit allows this facility to operate the equipment and air pollution control devices specified in this permit and 

emit up to a level specified for each source operation. The signatories named in the application are responsible for 

ensuring that the facility is operated in a manner consistent with this permit, its conditions, and applicable rules. 
Revision 4.8, 10/21/13 

Section B 

Facility Name: CARNEYS POINT GENERATING PLANT 

Facility ID No.: 65498 

Activity ID No.: BOP120002 

DEFINITIONS 

The terms used in this permit are used consistent with the definitions at N.J.A.C. 7:27-1 and N.J.A.C. 7:27-22. Any 

terms defined in this section are not defined at N.J.A.C. 7:27-1 or N.J.A.C. 7:27-22, and are needed for clarifying 

the permit. 

“Permitting Authority” means the New Jersey Department of Environmental Protection (NJDEP). 

“The EPA,” or “the Administrator,” means the Administrator of the EPA or his designee. 

“M” preceding a unit of measure means one thousand. For example, “10 M gal.” means ten thousand gallons. 

“MM” preceding a unit of measure means one million. For example, “10 MM gal.” means ten million gallons. 

“Grandfathered” means, in reference to equipment or control apparatus, that construction, reconstruction, or 

modification occurred prior to enactment of N.J.S.A. 26:2C-9.2 on June 15, 1967, or prior to the subsequent 

applicable revisions to rules and regulations codified at N.J.A.C. 7:27-8 that occurred March 5, 1973, June 1, 1976, 

April 5, 1985, and October 31, 1994, and no construction, reconstruction, or modification of the equipment or 

control apparatus has occurred since. 

“Compliance Plan” means the applicable requirements, monitoring requirements, recordkeeping requirements, and 

submittal/action requirements detailed in Section G, Facility Specific Requirements, of the operating permit. 
Revision 4.8, 10/21/13 

Section C 

Facility Name: CARNEYS POINT GENERATING PLANT 

Program Interest Number: 65498 

Permit Activity Number: BOP120002 

POLLUTANT EMISSIONS SUMMARY 

Table 1: Total emissions from all significant source operations at the facility. 

Facility’s Potential Emissions from all Significant Source Operations (tons per year) 

Source 

Categories 

Primary Secondary 

VOC 

(total) NOx CO SO2

TSP 

(total) 

Other* 

(total) 

PM10

(total) 

PM2.5

(total) Pb HAPs* (total) CO2e1

Emission Units 

Summary 44.1 1832 1344 2689 221.5 87.6 221.5 221.5 0.35 180 

Batch Process 

Summary NA NA NA NA NA NA NA NA NA NA 

Group 

Summary NA NA NA NA NA NA NA NA NA NA 

Total 

Emissions from 

Significant 

Source 

Operations2

44.1 1832 1344 2689 221.5 87.6 221.5 221.5 0.35 180 2,529,224 

Table 2: Estimate of total emissions from all insignificant source operations and total emissions from Non-Source 

Fugitives at the facility. 

Emissions from all Insignificant Source Operations and Non-Source Fugitive Emissions (tons per year) 

Source 

Categories 

Primary Secondary 

VOC 

(total) NOx CO SO2

TSP 

(total) 

Other 

(total) 

PM10

(total) 

PM2.5

(total) Pb HAPs (total) 

Estimate of 

Total 

Emissions from 

Insignificant 

Source 

Operations2

0.4 NA NA NA 7 NA 7 7 NA NA 

Total NonSource Fugitive 

Emissions3

NA NA NA NA 1.1 NA 0.3 0.3 NA NA 

VOC: Volatile Organic Compounds TSP: Total Suspended Particulates PM2.5: Particulates under 2.5 microns

NOx: Nitrogen Oxides Other: Any other air contaminant Pb: Lead 

CO: Carbon Monoxide regulated under the Federal CAA HAPs: Hazardous Air Pollutants 

SO2: Sulfur Dioxide PM10:Particulates under 10 microns CO2e: Carbon Dioxide equivalent 

*Emission summary of individual HAPs and Other Air Contaminants is provided on next page. 

 

1

 Total CO2e emissions for the facility that includes all significant sources (emission units, batch process, group) and 

insignificant sources. 

2

 Significant Source Operations and Insignificant Source Operations are defined at N.J.A.C 7:27-22.1. 3

Non-Source fugitive emissions are defined at N.J.A.C 7:27-22.1 and are included if the facility falls into one or 

more categories listed at N.J.A.C 7:27-22.2(a)2. 
Revision 4.8, 10/21/13 

Section C 

Facility Name: CARNEYS POINT GENERATING PLANT 

Program Interest Number: 65498 

Permit Activity Number: BOP120002 

POLLUTANT EMISSIONS SUMMARY 

The following table shows the hazardous air pollutants (HAP) emissions summary4: 

HAP TPY 

Arsenic 1.024 

Beryllium 0.05 

Cadmium 0.026 

Chromium 0.446 

Cobalt 1.7 

Formaldehyde 2.7 

Hydrogen Chloride 91.4 

Hydrogen Flouride 24.4 

Lead 0.35 

Manganese 13.1 

Mercury 0.0132 

Nickel 10.5 

Phosphorus 27.6 

Polycyclic Organic Matter 0.22 

Selenium 6.3 

The following table shows the “Other” air contaminants emissions summary: 

Other Air Contaminant TPY 

Ammonia 87.6 

 

 

4

 Do not sum the values below for the purpose of establishing a total HAP potential to emit. See previous page for 

the allowable total HAP emissions. 
Revision 4.8, 10/21/13 

Section D 

Facility Name: CARNEYS POINT GENERATING PLANT 

Facility ID No.: 65498 

Activity ID No.: BOP120002 

POLLUTION PREVENTION REPORTING 

General Pollution Prevention Conditions 

The following evaluation requirements are included to track the facility’s progress in several critical areas identified 

in the National Environmental Performance Partnership System (NEPPS). Nitrogen Oxides (NOx) and Volatile 

Organic Compounds (VOC) are precursors to the air pollutant Ozone, for which New Jersey is non-attainment with 

the air quality standard for the protection of public health. The control of hazardous air pollutants (HAPs) is also a 

focus item for the next decade in order to minimize localized hot spots and general urban air toxics levels. 

Therefore, the Department is requiring evaluation of emission trends at 5-year intervals for major sources of these 

air contaminants. Also, as part of significant modification applications, proposed major increases of these air 

contaminants requires evaluation of pollution prevention and cross media effects. 

The evaluation of these trends requires no increased monitoring. Rather it utilizes existing monitoring data, as 

reported annually in Emission Statements (for NOx and VOC) and annual Release and Pollution Prevention Reports 

(for HAPs). The intent of this evaluation is to better utilize the existing data by having the company, the public and 

the Department review major source trends periodically, as part of the 5-year renewal review and public comment 

process. The Department requests that the facility-wide trends be presented on graphs for attachment to the public 

information document for the 5-year renewal. 

Pollution prevention includes changes that result in the reduction in use or generation of non-product output per unit 

of product. Cross media effects are practices that result in transferring the ultimate release or disposal of a 

contaminant from one environmental medium (e.g. air) to another environmental medium (e.g. water, solid or 

hazardous wastes). 

Information to include with the renewal application: 

1. The facility will evaluate annual emission trends over the last five years for actual air contaminant 

emissions of Volatile Organic Compounds (VOC), Nitrogen Oxides (NOx), if the facility’s potential to 

emit VOC or NOx is greater than 25 tons per year, or any Hazardous Air Pollutants (HAP), for which the 

facility’s potential to emit is greater than 10 tons per year. The VOC and NOx emission data should reflect 

annual emission statement reports submitted pursuant to N.J.A.C. 7:27-21, and the HAP emissions data 

should reflect the annual Release and Pollution Prevention Report submitted pursuant to N.J.A.C. 7:1G-4 

and 5 and N.J.A.C. 7:1K-6. Although not required, the Department encourages the facility to explain the 

reason for any significant trend, including whether it is the result of cross media shifts (to air, water, or 

solid waste) and/or pollution prevention. Changes should be itemized for each emission unit (or process) 

with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton per year 

of any HAP. Also, show the net change for the facility. 

2. The facility will summarize annual potential to emit limits (allowable emissions) for VOC, NOx, and 

HAPs, which are subject to reporting under 1 above, for the last five years. Changes should be itemized for 

each emission unit (or process) with a potential to emit over five tons per year of VOC or NOx or a 

potential to emit over one ton per year of any HAP. Also, show the net change for the facility. 

3. The facility will summarize five-year trends in annual VOC, NOx, and HAP emissions, which are subject 

to reporting under 1 above, on a pound per unit of product basis, based on annual actual emissions and 

annual production over the five year period. Changes should be itemized for each emission unit (or 
Revision 4.8, 10/21/13 

process) with a potential to emit over five tons per year of VOC or NOx or a potential to emit over one ton 

per year of any HAP. Also, show the net change for the facility. 

4. The facility will discuss five-year trends in actual air contaminant emissions of non-source VOC and HAP 

fugitives, which are subject to reporting under 1 above; explain measures taken to minimize such fugitives; 

and provide an explanation for any significant changes. 

Information to include with an application for a Significant Modification to this permit: 

1. For any significant modifications, the facility is encouraged to explain any cross media shifts of VOC and 

HAP air contaminants as part of the significant modification application. If an explanation is provided, the 

facility should identify the pollutant and the specific environmental media to which the pollutant is 

anticipated to be transferred, whether it be from air to solid waste or water, or from water or solid waste to 

the air. 
Revision 4.8, 10/21/13 

Section E 

Facility Name: CARNEYS POINT GENERATING PLANT 

Facility ID No.: 65498 

Activity ID No.: BOP120002 

GENERAL PROVISIONS AND AUTHORITIES 

Operating Permits

1. No permittee shall allow any air contaminant, including an air contaminant detectable by the sense of 

smell, to be present in the outdoor atmosphere in a quantity and duration which is, or tends to be, injurious 

to human health or welfare, animal or plant life or property, or which would unreasonably interfere with the 

enjoyment of life or property. This shall not include an air contaminant which occurs only in areas over 

which the permittee has exclusive use or occupancy. Conditions relative only to nuisance situations, 

including odors, are not considered Federally enforceable. [N.J.A.C. 7:27-22.16(g)8] 

2. Any deviation from operating permit requirements which results in a release of air contaminants shall be 

reported to the Department as follows: 

If the air contaminants are released in a quantity or concentration which poses a potential threat to public 

health, welfare or the environment or which might reasonably result in citizen complaints, the permittee 

shall report the release to the Department: 

i. Immediately on the Department hotline at 1-877-927-6337, pursuant to N.J.S.A. 26:2C-19(e); and 

ii. As part of the compliance certification required in N.J.A.C. 7:27-22.19(f). However, if the 

deviation is identified through source emissions testing, it shall be reported through the source 

emissions testing and monitoring procedures at N.J.A.C. 7:27-22.18(e)3; or 

If the air contaminants are released in a quantity or concentration which poses no potential threat to public 

health, welfare or the environment and which will not likely result in citizen complaints, the permittee shall 

report the release to the Department as part of the compliance certification required in N.J.A.C. 7:27-

22.19(f), except for deviations identified by source emissions testing reports, which shall be reported 

through the procedures at N.J.A.C. 7:27-22.18(e)3; or 

If the air contaminants are released in a quantity or concentration which poses no potential threat to public 

health, welfare or the environment and which will not likely result in citizen complaints, and the permittee 

intends to assert the affirmative defense afforded by N.J.A.C. 7:27-22.16(l), the violation shall be reported 

by 5:00 P.M. of the second full calendar day following the occurrence, or of becoming aware of the 

occurrence, consistent with N.J.A.C. 7:27-22.16(l). [N.J.A.C. 7:27-22.19(g)] 

3. The permittee shall comply with all conditions of the operating permit including the approved compliance 

plan. Any non-compliance with a permit condition constitutes a violation of the New Jersey Air Pollution 

Control Act N.J.S.A. 26:2C-1 et seq., or the CAA, 42 U.S.C. §7401 et seq., or both, and is grounds for 

enforcement action; for termination, revocation and reissuance, or for modification of the operating permit; 

or for denial of an application for a renewal of the operating permit. [N.J.A.C. 7:27-22.16(g)1] 

4. It shall not be a defense for the permittee in an enforcement action that it would have been necessary to halt 

or reduce the permitted activity in order to maintain compliance with the conditions of its operating permit. 

[N.J.A.C. 7:27-22.16(g)2] 
Revision 4.8, 10/21/13 

5. This operating permit may be modified, terminated, or revoked for cause by the EPA pursuant to 40 CFR 

70.7(g) and revoked or reopened and modified for cause by the Department pursuant to N.J.A.C. 7:27-

22.25. [N.J.A.C. 7:27-22.16(g)3] 

6. The permittee shall furnish to the Department, within a reasonable time, any information that the 

Department may request in writing to determine whether cause exists for modifying, revoking and 

reissuing, or terminating this operating permit; or to determine compliance with the operating permit. 

[N.J.A.C. 7:27-22.16(g)4] 

7. The filing of an application for a modification of an operating permit, or of a notice of planned changes or 

anticipated non-compliance, does not stay any operating permit condition. [N.J.A.C. 7:27-22.16(g)5] 

8. The operating permit does not convey any property rights of any sort, or any exclusive privilege. [N.J.A.C. 

7:27-22.16(g)6] 

9. Upon request, the permittee shall furnish to the Department copies of records required by the operating 

permit to be kept. [N.J.A.C. 7:27-22.16(g)7] 

10. The Department and its authorized representatives shall have the right to enter and inspect any facility 

subject to N.J.A.C. 7:27-22, or portion thereof, pursuant to N.J.A.C. 7:27-1.31. [N.J.A.C. 7:27-22.16(g)9] 

11. The permittee shall pay fees to the Department pursuant to N.J.A.C. 7:27. [N.J.A.C. 7:27-22.16(g)10] 

12. Each permittee shall maintain records of all source emissions testing or monitoring performed at the facility 

and required by the operating permit in accordance with N.J.A.C. 7:27-22.19. Records shall be maintained, 

for at least five years from the date of each sample, measurement, or report. Each permittee shall maintain 

all other records required by this operating permit for a period of five years from the date each record is 

made. At a minimum, source emission testing or monitoring records shall contain the information specified 

at N.J.A.C. 7:27-22.19(b). [N.J.A.C. 7:27-22.19(a) and N.J.A.C. 7:27-22.19(b)] 

13. In accordance with N.J.A.C. 7:27-22.19(c) and 22.19(d) 3, each permittee shall submit to the Department a 

six month deviation report relating to testing and monitoring required by the operating permit, not 

including information for testing and monitoring which have other reporting schedules specified in the 

permit. Normally, stack testing reporting is submitted within 45 days of test completion and continuous 

monitoring reporting is done quarterly. The six month report must address other specified monitoring, 

including, but not limited to, continuous and periodic monitoring data required by this permit. (See column 

two and three entitled "Monitoring Requirement" and "Recordkeeping Requirement," respectively, in the 

Facility Specific Requirement Section of this permit.). The six month reports for the testing and 

monitoring performed from January 1 through June 30, shall be reported by July 30 of the same calendar 

year; or from July 1 through December 31, shall be reported by January 30 of the following calendar year. 

Pursuant to N.J.A.C. 7:27-22.19(e), these six month reports shall clearly identify all deviations from 

operating permit requirements, the probable cause of such deviations, and any corrective actions taken. 

Any "None" listed in the Submittal/Action Requirement in the Operating Permit is not intended to override 

the six-month deviation report. The report shall be certified pursuant to N.J.A.C. 7:27-1.39 by a 

responsible official. The submittal procedure is listed in column entitled “Submittal/Action Requirement” 

in the Facility Specific Requirement Section FC of this permit. [N.J.A.C. 7:27-22.19(d) 3 and N.J.A.C. 

7:27-22.19(e)] 

An annual compliance certification required by paragraph 2 above and required by N.J.A.C. 7:27-19(f) may 

also be considered as your six month deviation report for the period from July 1 through December 31 

which is due by January 30 of each year if the annual compliance certification is submitted by January 30. 

14. For emergencies (as defined at 40 CFR 70.6(g)(1)) that result in non-compliance with any promulgated 

federal technology-based standard such as NSPS, NESHAPS, or MACT, a federal affirmative defense is 

available, pursuant to 40 CFR 70. To assert a federal affirmative defense, the permittee must use the 

procedures set forth in 40 CFR 70. The affirmative defense provisions described in 15 below may not be 
Revision 4.8, 10/21/13 

applied to any situation that caused the Facility to exceed any federally delegated regulation, including but 

not limited to NSPS, NESHAP, or MACT. 

15. For situations other than those covered by 14 above, an affirmative defense is available for a violation of a 

provision or condition of the operating permit only if: 

i. The violation occurred as a result of an equipment malfunction, an equipment start-up or 

shutdown, or during the performance of necessary equipment maintenance; and 

ii. The affirmative defense is asserted and established as required by N.J.S.A. 26:2C-19.1 through 

19.5 and any implementing rules. [N.J.A.C. 7:27-22.16(l)] 

16. Each permittee shall meet all requirements of the approved source emissions testing and monitoring 

protocol during the term of the operating permit. [N.J.A.C. 7:27-22.18(j)] 

17. Unless specifically exempted from permitting, temporary mobile equipment for short-term activities may 

be periodically used at major facilities, on-site for up to 90 days if the requirements listed below, (a) 

through (h) are satisfied. 

a. The permittee will ensure that the temporary mobile equipment will not be installed permanently or 

used permanently on site. 

b. The permittee will ensure that the temporary mobile equipment will not circumvent any State or 

Federal rules and regulations, even for a short period of time, and the subject equipment will comply 

with all applicable performance standards. 

c. The permittee cannot use temporary mobile equipment unless the owner of the subject equipment has 

obtained and maintains an approved mobile preconstruction permit, issued pursuant to N.J.A.C. 7:27-8, 

prior to bringing the temporary mobile equipment to operate at the major facility. 

d. The permittee is responsible for ensuring the temporary mobile equipment’s compliance with the terms 

and conditions specified in its approved mobile preconstruction permit when the temporary mobile 

equipment operates on the property of the permittee. 

e. The permittee will ensure that temporary mobile equipment utilized for short-term activities will not 

operate on site for more than a total of ninety (90) days during any calendar year. 

f. The permittee will keep on site a list of temporary mobile equipment being used at the facility with the 

start date, end date, and record of the emissions from all such equipment (amount and type of each air 

contaminant) no later than 30 days after the temporary mobile equipment completed its job in 

accordance with N.J.A.C. 7:27-22.19(i) 3. 

g. Emissions from the temporary mobile equipment must be included in the emission netting analysis 

required of the permittee by N.J.A.C. 7:27-18.7. This information is maintained on-site by the 

permittee and provided to the Department upon request in accordance with existing applicable 

requirements in the FC Section of its Title V permit. 

h. Where short-term activities (employing temporary mobile equipment) will re-occur on at least an 

annual basis, the permittee is required to include such activities (and the associated equipment) within 

one year of the first use, in its Title V permit through the appropriate modification procedures. 

18. Each owner and each operator of any facility, source operation, or activity to which this permit applies is 

responsible for ensuring compliance with all requirements of N.J.A.C. 7:27-22. If the owner and operator 

are separate persons, or if there is more than one owner or operator, each owner and each operator is jointly 

and severally liable for any fees due under N.J.A.C. 7:27-22, and for any penalties for violation of N.J.A.C. 

7:27-22. [N.J.A.C. 7:27-22.3] 
Revision 4.8, 10/21/13 

19. In the event of a challenge to any part of this operating permit, all other parts of the permit shall continue to 

be valid. [N.J.A.C. 7:27-22.16(f)] 

20. The permittee shall ensure that no air contaminant is emitted from any significant source operation at a rate, 

calculated as the potential to emit, that exceeds the applicable threshold for reporting emissions set forth in 

the Appendix to N.J.A.C. 7:27-22, unless emission of the air contaminant is authorized by this operating 

permit. [N.J.A.C. 7:27-22.3(c)] 

21. Consistent with the provisions of N.J.A.C. 7:27-22.3(e), the permittee shall ensure that all requirements of 

this operating permit are met. In the event that there are multiple emission limitations, monitoring, 

recordkeeping, and/or reporting requirements for a given source operation, the facility must comply with all 

requirements, including the most stringent. 

22. Consistent with the provisions of N.J.A.C. 7:27-22.9(c), the permittee shall use monitoring of operating 

parameters, where required by the compliance plan, as a surrogate for direct emissions testing or 

monitoring, to demonstrate compliance with applicable requirements. 

23. The permittee shall file a timely and complete application for: 

Administrative Amendments [N.J.A.C. 7:27-22.20(c)]; 

Seven-Day-Notice changes [N.J.A.C. 7:27-22.22(e)]; 

Minor Modifications [N.J.A.C. 7:27-22.23(e)]; 

Significant Modifications [N.J.A.C. 7:27-22.24(e)]; and 

Renewals [N.J.A.C. 7:27-22.30(b)]. 

24. Except as allowed in Technical Manual 1005, or otherwise allowed by the Department in this permit or in 

written guidelines/ procedures issued or approved by the Department, process monitors required by the 

Compliance Plan included in this permit must be operated at all times when the associated process 

equipment is operating. The permittee must keep a service log to document any outage. 
Revision 4.8, 10/21/13 

Section F 

Facility Name: CARNEYS POINT GENERATING PLANT 

Facility ID No.: 65498 

Activity ID No.: BOP120002 

STATE-ONLY APPLICABLE REQUIREMENTS 

N.J.A.C. 7:27-22.16(b)5 requires the Department to specifically designate as not being federally enforceable any 

permit conditions based only on applicable state requirements. The applicable state requirements to which this 

provision applies are listed in the table titled “State-Only Applicable Requirements.” 

STATE-ONLY APPLICABLE REQUIREMENTS 

The following applicable requirements are not federally enforceable: 

 SECTION SUBJECT ITEM ITEM # REF. # 

 E --- 15 --- 

 G FC --- 3 

 G FC --- 9 
Revision 4.8, 10/21/13 

Section G 

Facility Name: CARNEYS POINT GENERATING PLANT 

Facility ID No.: 65498 

Activity ID No.: BOP120002 

COMPLIANCE PLAN AND INVENTORIES 

• FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX 

• FACILITY SPECIFIC REQUIREMENTS (COMPLIANCE PLAN) 

• ATTACHMENTS TO THE FACILITY SPECIFIC REQUIREMENTS 

• FACILITY PROFILE (ADMINISTRATIVE INFORMATION) 

• REASON FOR APPLICATION 

• NON-SOURCE FUGITIVE EMISSIONS 

• INSIGNIFICANT SOURCE EMISSIONS 

• EQUIPMENT INVENTORY 

• EQUIPMENT DETAILS 

• CONTROL DEVICE INVENTORY 

• CONTROL DEVICE DETAILS 

• EMISSION POINT INVENTORY 

• EMISSION UNIT/BATCH PROCESS INVENTORY 

• SUBJECT ITEM GROUP INVENTORY 

• ADDITIONAL WORD/EXCEL/PDF DOCUMENTS

 
Revision 4.8, 10/21/13 

Facility Name: CARNEYS POINT GENERATING PLANT 

Facility ID No.: 65498 

Activity ID No.: BOP120002 

FACILITY SPECIFIC REQUIREMENTS – PAGE INDEX 

Subject Item and Name Page Number 

 Facility (FC): 

 FC 1

Non-Source Fugitive Emissions (FG): 

FG1 – Travel on Roads 7

FG2 – Coal Handling on Storage Pile 

FG3 – Wind Erosion from Storage Pile 

FG4 – Miscellaneous Coal Handling, FG5 Miscellaneous Ash Handling, and 

FG6 – Miscellaneous Lime and Dry Chemical Handling 

 

Insignificant Sources (IS):

 IS1 – Bottom Ash Handling (< 50 lb/hr raw materials processed) 11

 IS2 – Cooling Tower (< 50 lb/hr raw materials processed) 

 IS4 – Magnetic Separator (< 50 lbs/hr raw materials processed) 

 IS5 – Lime Grit Reject (< 50 lb/hr raw materials processed) 

 IS6 – Seal Oil/Lube Oil Vents w/Vapor Extractors (< 50 lb/hr throughput), 

 IS13 Boiler Cleaning (< 50 lbs/hr throughput), and IS14 Spray Dryer 

 Absorber Bottom Exhaust (< 50 lbs/hr throughput) 

 IS8 – Boiler Water Treatment – various steam vents (< 50 lb/hr throughput) 

 IS11 – Parts Washing (< 6 sq.ft. each) 

 IS15 – Distillate Fuel Oil Tanks (vapor pressure < 0.02 psia) 

 IS16 – Non-VOC Storage Tanks (> 10,000 gal) 

 Group (GR):

GR1 PC Boilers #1 and #2, Summary 21

 GR2 PC Boiler #1 and #2, Normal Firing Using Coal, No. 6 or No. 2 Oil 

 GR3 PC Boiler #1 and #2, Start-Up 

 GR4 PC Boiler #1 and #2, Shut-Down 

 GR5 Units U10, U11, U13, U14 and U18 

Unit (U): 

 U1 Ct 108170 – PC Boiler #1 62 

 OS Summary 

 U2 Ct 108169– PC Boiler #2 66 

 OS Summary 

 U3 Auxiliary Boiler 70 

 OS Summary 
Revision 4.8, 10/21/13 

 U10 Ct 115560 – Coal Unloader 84 

 OS Summary 

 U11 Ct 115560 – Apron Feeder & Stack-Out Conveyor Tail 87 

 OS Summary 

 U13 Ct 115562 – Reclaim Conveyor Tail 90 

 OS Summary 

 U14 Ct 099327 – 6700 Crusher Bldg. Bghse. 93 

 OS Summary 

 U18 Ct 115563 – Coal Silo Bay 99 

 OS Summary 

 

 U30 Ct 115564 – Ash Transfer System 111 

 OS Summary 

 U34 Ct 115558 – Ash Recycle Silo 114 

 OS Summary 

 U35 Ash Mixer normal operation (mix ash with water) 117 

 OS Summary 

 U36 Ct 115559 – Ash Storage Silo and Unloader 120 

 OS Summary 

 U37 Ct 099322 – Lime Silo 123 

 OS Summary 

 U38 Ct 117297 – Diesel Fire Pump 126 

 OS1 Detroit Diesel DDFP-06FA-8175 

 Note: See Attachments for additional requirements 
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: FC

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 General Provisions: Defines numerous terms

used in N.J.A.C. 7:27. Specifies proceduresfor making confidentiality claims, certifyingapplications, reports, and other documentsto the Department, and requestingadjudicatory hearings and stays of theeffective date of departmental decisions.Also, provides provisions regardingapplicability, severability, and liberalconstruction of N.J.A.C. 7:27. [N.J.A.C.7:27- 1]

None. None. None.

2 Control and Prohibition of Open Burning:

Prohibits any person from open burning ofrubbish, garbage, trade waste, buildings,structures, leaves, other plant life andsalvage. Open burning of infested plant lifeor dangerous material may only beperformed with a permit from theDepartment. [N.J.A.C. 7:27- 2]

None. None. Obtain an 

occurrence [N.J.A.C. 

3 Prohibition of Air Pollution:

Notwithstanding compliance with othersubchapters of N.J.A.C. 7:27, no personshall suffer, allow, or permit to be emittedinto the outdoor atmosphere substances inquantities that result in air pollution asdefined at N.J.A.C. 7:27-5.1. Applicable toall facilities located in New Jersey.[N.J.A.C. 7:27- 5]

None. None. None.

Page 1 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

4 Prevention and Control of Air Pollution

Control Emergencies: Requires that writtenStandby Plans, consistent with goodindustrial practice and safe operatingprocedures, be prepared for reducing theemission of air contaminants during periodsof an air pollution alert, warning, oremergency. Any person responsible for theoperation of a source of air contaminationnot set forth in Table 1 of N.J.A.C. 7:27-12is not required to prepare such a plan unlessrequested by the Department in writing.[N.J.A.C. 7:27-12]

None. None. Comply w

occurrence the Governwarning, oput the Stathe permitapplicable N.J.A.C. 7complied wpollution a[N.J.A.C. 

5 Emission Offsets Rules. [N.J.A.C. 7:27-18] Other: When applying for minor/significant

modification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [N.J.A.C. 7:27-18].

Comply woccurrence administraapplying fto N.J.A.Cmodificati7:27-22.24

6 Emissions Statements: Submit an annual

emission statement (if required)electronically to the NJDEP by May 15 ofeach year (or by mutually agreed upon date,but no later than June 15 of each year).[N.J.A.C. 7:27-21]

Other: The emission statement will be basedon monitoring, recording and recordkeepingof actual emissions, capture and controlefficiencies, process rate and operating datafor source operations with the potential toemit certain air contaminants. [N.J.A.C.7:27-21].

Other: The emission statement and allsupporting records shall be maintained onthe operating premises for a period of five(5) years from the due date of each emissionstatement. [N.J.A.C. 7:27-21].

Submit an Annually (15 or by anot later th[N.J.A.C. 

Page 2 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 Compliance Certification: Submit annual

compliance certification for each applicablerequirement, pursuant to N.J.A.C.7:27-22.19(f), within 60 days after the endof each calendar year during which thispermit was in effect. [N.J.A.C. 7:27-22]

None. None. Submit an 

Annually t60 days afduring whannual comperiod wilDecember submitted online web Certificatipursuant tresponsiblonline web following http://wwwcertificatiosubmissio [N.J.A.C

8 Prevention of Air Pollution from Consumer

Products and Architectural Coatings.[N.J.A.C. 7:27-24] and [N.J.A.C. 7:27-23]

None. None. None.

9 Any operation of equipment which causes

off-property effects, including odors, orwhich might reasonably result in citizen'scomplaints shall be reported to theDepartment to the extent required by the AirPollution Control Act, N.J.S.A.26:2C-19(e). [N.J.S.A. 26: 2C-19(e)]

Other: Observation of plant operations.[N.J.S.A. 26: 2C-19(e)].

Other: Maintain a copy of all informationsubmitted to the Department. [N.J.S.A. 26:2C-19(e)].

Notify by A person wcontaminawhich poshealth, wemight reasshall immeSuch notifthe Enviro927-6337. 

10 Prevention of Significant Deterioration

(PSD). [40 CFR 52.21]

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].

Other: When applying for minor/significantmodification, demonstrate compliance withthis applicable requirement which may callfor specific monitoring and/orrecordkeeping activities. [40 CFR 52.21].

Comply woccurrence permittee complete asignificant N.J.A.C. 7

Page 3 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

11 National Emission Standards for Hazardous

Air Pollutants (NESHAPS) for Asbestos. [40 CFR 61]

Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].

Other: Comply with 40 CFR 61.145 and61.150 when conducting any renovation ordemolition activities at the facility. [40 CFR61].

Comply woccurrence comply wiwhen conddemolition 61]

12 Protection of Stratospheric Ozone:1) If the

permittee manufactures, transforms,destroys, imports, or exports a Class I orClass II substance, the permittee is subjectto all the requirements as specified at 40CFR 82, Subpart A; 2) If the permitteeperforms a service on motor "fleet" vehicleswhen this service involves an ozonedepleting substance refrigerant (or regulatedsubstance) in the motor vehicle airconditioner (MVAC), the permittee issubject to all the applicable requirements asspecified at 40 CFR 82, Subpart B. 3) Thepermittee shall comply with the standardsfor labeling of products containing ormanufactured with ozone depletingsubstances pursuant to 40 CFR 82, SubpartE. 4). The permittee shall comply with thestandards for recycling and emissionreductions of Class I and Class IIrefrigerants or a regulated substitutesubstance during the service, maintenance,repair, and disposal of appliances pursuantto 40 CFR 82, Subpart F, except as providedfor motor vehicle air conditioners (MVACs)in Subpart B. 5) The permittee shall beallowed to switch from any ozone depletingsubstance to any alternative that is listed inthe Significant New Alternative Program(SNAP) promulgated pursuant to 40 CFR82, Subpart G. [40 CFR 82]

Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].

Other: Comply with 40 CFR 82 Subparts A,B, E, F, and G. [40 CFR 82].

Comply woccurrence comply wiF, and G. 

Page 4 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

13 Deviation Report: In accordance with

N.J.A.C. 7:27-22.19(c) and 22.19(d)3, thepermittee shall submit to the Department acertified six-month deviation report relatingto testing and monitoring required by theoperating permit, not including informationfor stack emissions testing or continuousemissions monitoring which have otherreporting schedules specified in the permit(normally, stack test report is submittedwithin 45 days of test completion andcontinuous monitor reporting is donequarterly). Pursuant to N.J.A.C.7:27-22.19(e), the six-month report mustaddress other specified monitoring,including continuous and periodicmonitoring requirements found in column 2and 3, entitled "Monitoring Requirement"and "Recordkeeping Requirement,"respectively, of the Facility SpecificRequirements section of this permit. Thesesix-month reports shall clearly identify alldeviations from operating permitrequirements, the probable cause of suchdeviations, and any corrective actions orpreventive measures taken. If no deviationsoccurred, the report should say so. Any"None" listed in the Submittal/ActionRequirement in the Operating Permit is notintended to override the six-month deviationreport. [N.J.A.C. 7:27-22.19(d)3, N.J.A.C.7:27-22.19(e), and [N.J.A.C. 7:27-22.19(c)]

None. Other: The permittee shall maintain

deviation reports for a period of five yearsfrom the date each report is submitted to theDepartment. [N.J.A.C. 7:27-22.19(a)].

Submit a rschedule. specified tthe operatiJanuary 1 submitted year, and fshall be sufollowing submitted online web Certificatipursuant tresponsiblonline web following http://www[N.J.A.C. 

14 No person shall combust used oil except as

authorized pursuant to N.J.A.C. 7:27-20.[N.J.A.C. 7:27-20.2]

None. None. Comply w

occurrence oil) either pursuant tpermit issto N.J.A.Capplicable

Page 5 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

15 Prevention of Accidental Releases: Facilities

producing, processing, handling or storing achemical, listed in the tables of 40 CFR Part68.130, and present in a process in aquantity greater than the listed ThresholdQuantity, shall comply with 40 CFR 68. [40CFR 68]

Other: Comply with 40 CFR 68. [40 CFR68].

Other: Comply with 40 CFR 68. [40 CFR68].

Other (prowith 40 CFApplicable 

Page 6 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: FG1 Travel on Roads

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Fugitive emissions from all permanent

facility access roads for the plant on facilityproperty shall be controlled by paving androad cleaning. [N.J.A.C. 7:27-22.16(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-22.16(o)].

None. None.

Page 7 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: FG2 Coal Handling on Storage Pile

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Inactive coal stockpiles shall be moistened

or treated (wet suppression and/orsurfactant) and the inactive stockpilesurfaces shall be kept moist or otherwisetreated at all times to minimize fugitiveemissions during storage. The surfactantspray to be used for wet suppression of coaldust must be water or nonpetroleum basesurfactant. [N.J.A.C. 7:27-22.16(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-22.16(o)].

None. None.

Page 8 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: FG3 Wind Erosion from Storage Pile

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Inactive coal stockpiles shall be moistened

or treated (wet suppression and/orsurfactant) and the inactive stockpilesurfaces shall be kept moist or otherwisetreated at all times to minimize fugitiveemissions during storage. The surfactantspray to be used for wet suppression of coaldust must be water or nonpetroleum basesurfactant. [N.J.A.C. 7:27-22.16(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-22.16(o)].

None. None.

Page 9 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: FG4 Miscellaneous Coal Handling, FG5 Miscellaneous Ash Handling, FG6 Miscellaneous Lime & Dry Chemical H

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 There shall be no visible fugitive emissions

to the outdoor air from the coal, ash, andlime handling operations. [N.J.A.C.7:27-22.16(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-22.16(o)].

None. None.

Page 10 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS1 Bottom ash handling (< 50 lb/hr raw materials processed)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity may be no greater than 20%,

exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30-minuteperiod. Opacity <= 20% [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-6.2(d)] &[N.J.A.C. 7:27-6.2(e)].

None. None.

2 There shall be no visible emissions to the

outdoor air from the coal, ash, and limehandling operations. [N.J.A.C.7:27-22.16(a)]

Other: Periodic visual inspections.[N.J.A.C.7:27-22.16(o)].

None. None.

Page 11 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS2 Cooling Tower (< 50 lbs/hr raw materials processed)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity may be no greater than 20%,

exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30-minuteperiod. Opacity <= 20% [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-6.2(d)] &[N.J.A.C. 7:27-6.2(e)].

None. None.

2 Water treatment chemicals containing

hexavalent chromium shall not be added tothe cooling tower circulating water.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 12 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS4 Magnetic Separator (< 50 lb/hr raw materials processed)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity may be no greater than 20%,

exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30-minuteperiod. Opacity <= 20% [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-6.2(d)] &[N.J.A.C. 7:27-6.2(e)].

None. None.

2 There shall be no visible emissions to the

outdoor air from the coal, ash, and limehandling operations. [N.J.A.C.7:27-22.16(a)]

Other: Periodic visual inspections.[N.J.A.C.7:27-22.16(o)].

None. None.

Page 13 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS5 Lime Grit Reject (< 50 lb/hr raw materials processed)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity may be no greater than 20%,

exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30-minuteperiod. Opacity <= 20% [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-6.2(d)] &[N.J.A.C. 7:27-6.2(e)].

None. None.

2 There shall be no visible emissions to the

outdoor air from the coal, ash, and limehandling operations. [N.J.A.C.7:27-22.16(a)]

Other: Periodic visual inspections.[N.J.A.C.7:27-22.16(o)].

None. None.

Page 14 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS6 Seal Oil/ Lube Oil Vents w/ vapor extractors (< 50 lb/hr throughput), IS13 Boiler cleaning (< 50 lbs/hr throug

Absorber Bottom Exhaust (< 50 lbs/hr throughput)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity may be no greater than 20%,

exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30-minuteperiod. Opacity <= 20% [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-6.2(d)] &[N.J.A.C. 7:27-6.2(e)].

None. None.

Page 15 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS8 Boiler Water Treatment - various steam vents (< 50 lbs/hr throughput)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Opacity may be no greater than 20%,

exclusive of visible condensed water vapor,except for a period of not longer than threeminutes in any consecutive 30-minuteperiod. Opacity <= 20% [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

Other: Periodic visual inspections.[N.J.A.C.7:27-6.2(d)] &[N.J.A.C. 7:27-6.2(e)].

None. None.

Page 16 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS11 Parts washing (< 6 sqft, each)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Surface cleaner shall be covered by a lid that

protects the VOC vapors from drafts anddiffusion when tank is not in active use.[N.J.A.C. 7:27-16.6(a)]

Other: Ensure that the surface cleaner iscovered with a lid when not in use.[N.J.A.C.7:27-16.6(a)].

None. None.

2 Written operating, inspection, and

maintenance instructions, prepared inaccordance with the Department'sguidelines, must be followed. [N.J.A.C.7:27-16.6(j)]

None. None. None.

3 Maintain a training program to ensure that

all personnel associated with the use oroperation of the open tank or surface cleanerunderstand and follow the specifiedprocedure. [N.J.A.C. 7:27-16.6(k)]

None. None. None.

4 Copies of operating and maintenance

instructions must be located at the open toptank or surface cleaner. [N.J.A.C.7:27-16.6(l)]

None. None. None.

5 Notify the Department in writing within 15

days of any revision or alteration of aprocedure approved by the Department. Thenotification shall include a detaileddescription of the changes in the procedureand the reasons therefor. [N.J.A.C.7:27-16.6(n)]

None. None. None.

6 No halogenated solvents are to be used in

this equipment. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by formulation data at theapproved frequency, based on no averagingperiod. At the time of filling, confirm byMSDS or bill of lading.[N.J.A.C.7:27-22.16(o)].

Other: Recordkeeping by invoices/bills oflading at the approved frequency (per filling,showing materials beingdelivered).[N.J.A.C. 7:27-22.16(o)].

None.

Page 17 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS15 Distillate Fuel Oil Tanks (< 0.02 psia vapor pressure)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Sulfur Content in Fuel <= 500 ppmw. If the

tank contains distillate fuel for use in SalemCounty New Jersey (Zone 5), the maximumallowable sulfur content is 500 ppm byweight. (Effective through June 30, 2016).[N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery, basedon no averaging period. The permittee shallcheck the fuel oil sulfur content on theinvoices/bills of lading. [N.J.A.C.7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

2 Sulfur Content in Fuel <= 15 ppmw. If the

tank contains distillate fuel for use in SalemCounty New Jersey (Zone 5), the maximumallowable sulfur content is 15 ppm byweight. (Effective from July 1, 2016).[N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

3 If the tank contains No. 6 Fuel Oil for use in

Salem County New Jersey (Zone 5), themaximum allowable Sulfur Content in Fuel<= 5,000 ppmw. [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

4 The operating temperature shall not be

greater than 350 degrees F. [N.J.A.C.7:27-22.1]

None. None. None.

5 The vapor pressure of the liquid, excluding

the vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]

None. None. None.

6 The tank shall have no visible emissions,

exclusive of water vapor, to the outdooratmosphere. [N.J.A.C. 7:27-22.1]

None. None. None.

7 The tank shall not emit any air contaminants

which may cause an odor detectable outsidethe property boundaries of the facility.[N.J.A.C. 7:27-22.1]

None. None. None.

8 The tank's potential to emit each TXS and

each HAP shall not exceed the de minimisreporting thresholds as specified in N.J.A.C.7:27-22, Appendix. [N.J.A.C. 7:27-22.1]

None. None. None.

Page 18 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 The percentage by weight of all HAPs

collectively in the raw material stored in thetank shall be less than 1.0 percent. [N.J.A.C.7:27-22.1]

None. None. None.

10 The owner or operator shall have readily

available upon Department request astatement certified in accordance withN.J.A.C. 7:27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank meets theapplicable requirements of Ref. #4 to #9above and (3) attests that the tank is incompliance with all other applicable State orfederal air pollution requirements. [N.J.A.C.7:27-22.1]

None. None. None.

Page 19 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: IS16 Non-VOC Storage Tanks (> 10,000 gal)

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The operating temperature shall not be

greater than 350 degrees F. [N.J.A.C.7:27-22.1]

None. None. None.

2 The vapor pressure of the liquid, excluding

the vapor pressure of water, shall be lessthan 0.02 psia at the liquid's actualtemperature or at 70 degrees F, whichever ishigher. [N.J.A.C. 7:27-22.1]

None. None. None.

3 The tank shall have no visible emissions,

exclusive of water vapor, to the outdooratmosphere. [N.J.A.C. 7:27-22.1]

None. None. None.

4 The tank shall not emit any air contaminants

which may cause an odor detectable outsidethe property boundaries of the facility.[N.J.A.C. 7:27-22.1]

None. None. None.

5 The tank's potential to emit each TXS and

each HAP shall not exceed the de minimisreporting thresholds as specified in N.J.A.C.7:27-22, Appendix. [N.J.A.C. 7:27-22.1]

None. None. None.

6 The percentage by weight of all HAPs

collectively in the raw material stored in thetank shall be less than 1.0 percent. [N.J.A.C.7:27-22.1]

None. None. None.

7 The owner or operator shall have readily

available upon Department request astatement certified in accordance withN.J.A.C. 7:27-1.39, signed by theresponsible official, as defined at N.J.A.C.7:27-1.4, that: (1) specifies the contents ofthe tank; (2) affirms that the tank meets theapplicable requirements of Ref. #1 to #6above and (3) attests that the tank is incompliance with all other applicable State orfederal air pollution requirements. [N.J.A.C.7:27-22.1]

None. None. None.

Page 20 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: GR1 PC Boilers #1 & #2, Summary

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Annual heat input to the two PC boilers,

based on the preconstruction permit, is24,400,000 MMBtu (HHV)/any consecutive365 days. Total annual heat input duringany consecutive 365-day period shall becalculated by adding the total heat input tothe PC boilers for a given day to the totalheat input during the preceding 364-day

period.Daily MMBtu fuel use shall be calculatedusing the following formula:MMBtu/day = [( X tons bituminous coal x26 MMBtu/ton) + ( Y Mgal #6 fuel oil x150 MMBtu/Mgal) + ( Z Mgal #2 fuel oil x140 MMBtu/Mgal),where X, Y and Z = actual amounts ofbituminous coal, #6 fuel oil and #2 fuel oil,combusted daily, respectively.This procedure will begin the first dayfollowing the issuance of the OperatingPermit. This accounting will not includeheat input for the days prior to the OperatingPermit approval. [N.J.A.C. 7:27-22.16(e)]

Monitored by fuel flow/firing rateinstrument continuously, based on aconsecutive 365 day period (rolling 1 daybasis) and calculations. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. Compliance shall bedetermined based on a 365 consecutive dayperiod computed with daily sums. [N.J.A.C.7:27-22.16(o)]

Submit a rschedule , emission lshall be rethe close o7:27-22.16

Page 21 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

2 Conduct comprehensive stack emission

testing as follows:For coal firing, stack test for criteriapollutants (NOx, SO2, CO, VOC),ammonia, non-metals (P & Se), totaldioxins/furans, and POM (Naphthalene,Acenaphthene, Acenaphthylene, Fluorene,Phenanthrene, Anthracene, Fluoranthene,Pyrene, Benzo(ghi)perylene,Benz(a)anthracene, Chrysene,Benzo(b)fluoranthene,Benzo(k)fluoranthene, Benzo(a)pyrene,Dibenz(a,h)anthracene,Indeno(1,2,3-cd)pyrene) at least 18 monthsprior to the expiration of the approvedoperating permit to demonstrate compliancewith the emission limits.When stack testing, three consecutive runsshall be conducted at worst-case permittedoperating conditions with regard to meetingthe applicable emission standards, butwithout creating an unsafe condition. Heatinput (MMBtu/hr, HHV) shall bedetermined for each stack test. [N.J.A.C.7:27-22.16(e)]

Monitored by stack emission testing prior topermit expiration date. Stack testing shall beconducted for NOx, SO2, CO, VOC,ammonia, and HAPs, as applicable. (SeeApplicable Requirement). [N.J.A.C.7:27-22.16(o)]

Recordkeeping by stack test results prior topermit expiration date and certified labanalysis of fuel sampling. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. Bureau of Code: 38008625 at lexpiration The protocprepared aElectronic another foERT progrhttp://wwwWithin 30 less than 6deadline, wmust contaschedule a A full stacBTS and a must be suEnforcemeperforming N.J.A.C. 7must be ceengineer oTest resultlb/MMBTdioxins/fuppmvd @ matter, dioof all 16 Pspeciated 7:27-22.187:27-22.16

Page 22 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 Conduct comprehensive stack emission

testing as follows:For coal firing, stack tests for criteriapollutants (TSP & PM-10), heavy metals(As, Be, Cd, Cr, Co, Pb, Mn, Hg, Ni), andacid gases (HCl & HF) shall be conductedannually to demonstrate compliance with theemission limits.When stack testing, three consecutive runsshall be conducted at worst-case permittedoperating conditions with regard to meetingthe applicable emission standards, butwithout creating an unsafe condition. Heatinput (MMBtu/hr, HHV) shall bedetermined for each stack test. [N.J.A.C.7:27-22.16(e)]

Monitored by stack emission testingannually. Stack testing shall be conductedfor TSP, PM-10, and HAPs, as applicable.(See Applicable Requirement). [N.J.A.C.7:27-22.16(o)]

Recordkeeping by stack test results annuallyand certified lab analysis of fuel sampling.[N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. Bureau of Code: 38008625 by protocol aand submiReporting format is aprogram chttp://wwwdays of prdays prior is later, th609-530-4acceptable A full stacBTS and a must be suEnforcemeperforming N.J.A.C. 7must be ceengineer oTest resultlb/MMBTexcept for 7:27-22.187:27-22.16

4 No visible emissions greater than 20%

opacity, exclusive of condensed watervapor, except for a period of not longer thanthree minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-3.2(a)] & [N.J.A.C.7:27- 3.2(c)]

Monitored by continuous opacitymonitoring system continuously, based onany consecutive 30-minute period.[N.J.A.C.7:27-3.2(a)] &. [N.J.A.C. 7:27-3.2(c)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C.7:27-3.2(a)] &.[N.J.A.C. 7:27- 3.2(c)]

None.

Page 23 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

5 The permittee shall ensure that the operating

parameter settings are established andrecorded after the combustion process isadjusted and that the adjusted equipment orsource operation is maintained to operateconsistent with the annual adjustment.[N.J.A.C. 7:27-19.16(e)]

Other: Monitor and maintain the operatingparameter settings that are established afterthe combustion process is adjusted in orderto operate consistent with the annualadjustment.[N.J.A.C. 7:27-22.16(o)].

Other: The owner or operator shall recordthe operating parameter settings that areestablished after the combustion process isadjusted.[N.J.A.C. 7:27-19.16(o)].

None.

6 PC boiler fuels limited to bituminous coal,

#6 fuel oil and #2 fuel oil. [N.J.A.C.7:27-22.16(e)]

None. Other: Keep records of Invoices/Bills of

Lading Showing Materials Delivered. PerDelivery.[N.J.A.C. 7:27-22.16(a)].

None.

7 Particulate emission limit from the

combustion of fuel based on rated heat inputof source. Particulate Emissions <= 139lb/hr. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

8 Maximum gross heat input from

preconstruction permit. Maximum GrossHeat Input <= 1,389 MMBTU/hr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

9 Annual emission limit based on operating

permit application, per boiler. Nickelcompounds <= 5.24 tons/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

10 The owner or operator of any utility boiler

shall not exceed concentrations of CO <=100 ppmdv @ 7% O2. [N.J.A.C.7:27-16.8(b)2]

CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day and stack emission testingbased on the average of three one-hour tests.(See Applicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-16.8(b)2]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously and stack test results. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-16.8(b)2]

Stack Test and submischedule. for GR1 P[N.J.A.C. 

11 The owner or operator of any utility boiler

shall not exceed concentrations of VOC(Total) <= 50 ppmdv @ 7% O2. [N.J.A.C.7:27-16.8(b)1]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date basedon the average of three consecutiveone-hour tests. (See Applicable Requirementfor GR1 PCBoilSUM Reference # 2).[N.J.A.C. 7:27-16.8(b)1]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-16.8(b)1]

Stack Test and submischedule. for GR1 P[N.J.A.C. 

12 Annual emission limit based on

preconstruction permit, per boiler. Ammonia<= 43.8 tons/yr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 24 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

13 Annual emission limit based on operating

permit application, per boiler. Hydrogenchloride <= 45.7 tons/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

14 Annual emission limit based on

preconstruction permit, per boiler. Hydrogenfluoride <= 12.2 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

15 Annual emission limit per boiler. PM-2.5

(Total) <= 110 tons/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

16 Annual emission limit based on

preconstruction permit, per boiler. PM-10(Total) <= 110 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

17 An exceedance of an emission limit that

occurs during an adjustment of thecombustion process under N.J.A.C.7:27-19.16(a) is not a violation of N.J.A.C.7:27-19 if it occurs as a result of theadjustment. After the combustionadjustment has been completed, themaximum emission rate of any contaminantshall not exceed the maximum allowableemission rate applicable underN.J.A.C. 7:27-19 or under an operatingpermit issued pursuant to N.J.A.C. 7:27-22. [N.J.A.C. 7:27-19.16(f)]

None. None. None.

18 Annual emission limit based on

preconstruction permit, per boiler.Beryllium compounds <= 0.025 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

19 Annual emission limit based on

preconstruction permit, per boiler. Cadmiumcompounds <= 0.013 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

20 Annual emission limit based on

preconstruction permit, per boiler. Arseniccompounds <= 0.512 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

Page 25 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

21 Annual emission limit based on

preconstruction permit, per boiler.Chromium compounds <= 0.223 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

22 Annual emission limit based on operating

permit application, per boiler. Cobaltcompounds <= 0.84 tons/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

23 Annual emission limit based on

preconstruction permit, per boiler. Leadcompounds <= 0.175 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

24 Annual emission limit based on operating

permit application, per boiler. Manganesecompounds <= 6.55 tons/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

25 Annual emission limit based on operating

permit application, per boiler. Formaldehyde<= 1.35 tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

26 Annual emission limit based on operating

permit application, per boiler. Seleniumcompounds <= 3.16 tons/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

27 TSP <= 110 tons/yr per boiler. [N.J.A.C.

7:27-22.16(a)]

TSP: Monitored by calculations annually,based on a 12 calendar month period.[N.J.A.C. 7:27-22.16(o)]

TSP: Recordkeeping by manual logging ofparameter or storing data in a computer datasystem annually. [N.J.A.C. 7:27-22.16(o)]

None.

Page 26 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

28 Each owner or operator required to install a

continuous monitoring system (CMS) ormonitoring device shall submit an excessemissions and monitoring systemsperformance report (excess emissions aredefined in applicable subparts) and/or asummary report form (see 40 CFR 60.7(d))to the Administrator semiannually, exceptwhen: more frequent reporting isspecifically required by an applicablesubpart; or the CMS data are to be useddirectly for compliance determination, inwhich case quarterly reports shall besubmitted; or the Administrator, on acase-by-case basis, determines that morereporting is necessary to accurately assessthe compliance status of the source. [40CFR 60.7(c)]

None. Other: Written reports of excess emissions

shall include the following information:(1) The magnitude of excess emissionscomputed in accordance with 40 CFR60.13(h), any conversion factor(s) used, andthe date and time of commencement andcompletion of each time period excessemissions. The process operating timeduring the reporting period.(2) Specific identification of each period ofexcess emissions that occurs duringstart-ups, shutdowns, and malfunctions ofthe affected facility. The nature and causeof any malfunction (if known), thecorrective action taken or preventativemeasures adopted.(3) The date and time identifying eachperiod during which the continuousmonitoring system was inoperative exceptfor zero and span checks and the nature ofthe system repairs or adjustments.(4) When no excess emissions have occurredor the continuous monitoring system(s) havenot been inoperative, repaired, or adjusted,such information shall be stated in thereport.[40 CFR 60.7(c)].

Submit an Monitorin(EEMPR)30, and Jayear (the qApril 1, Juthrough thportal.The report format as and 40 CFThe reportRegion II Regional ECFR 60.7(

29 Copies of all information submitted to the

EPA pursuant to 40 CFR Part 60, shall alsobe submitted to NJDEP.[40 CFR 60.4(b)]

None. None. Submit a r

schedule , Regional E40 CFR 60The addreSouthern RNJDEPOne Port C2 RiversidCamden, N

Page 27 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

30 Annual emission limit based on operating

permit application, per boiler. Phosphorus<= 13.8 tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

31 Mercury compounds <= 0.0066 tons/yr per

boiler. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

32 VOC (Total) <= 21.9 tons/yr per boiler.

[N.J.A.C. 7:27-22.16(a)]

VOC (Total): Monitored by calculationsannually, based on a 12 calendar monthperiod. [N.J.A.C. 7:27-22.16(o)]

VOC (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system annually. [N.J.A.C.7:27-22.16(o)]

None.

33 SO2 <= 1,339 tons/yr per boiler. [N.J.A.C.

7:27-22.16(a)]

SO2: Monitored by calculations annually,based on a 12 calendar month period.[N.J.A.C. 7:27-22.16(o)]

SO2: Recordkeeping by manual logging ofparameter or storing data in a computer datasystem annually. [N.J.A.C. 7:27-22.16(o)]

None.

34 CO <= 669 tons/yr per boiler. [N.J.A.C.

7:27-22.16(a)]

CO: Monitored by calculations annually,based on a 12 calendar month period.[N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by manual logging ofparameter or storing data in a computer datasystem annually. [N.J.A.C. 7:27-22.16(o)]

None.

35 NOx (Total) <= 913 tons/yr per boiler.

[N.J.A.C. 7:27-22.16(a)]

NOx (Total): Monitored by calculationsannually, based on a 12 calendar monthperiod. [N.J.A.C. 7:27-22.16(o)]

NOx (Total): Recordkeeping by manuallogging of parameter or storing data in acomputer data system annually. [N.J.A.C.7:27-22.16(o)]

None.

36 All requests, reports, applications,

submittals, and other communicationspursuant to 40 Part 60 shall be submitted induplicate to the EPA Region IIAdministrator. [40 CFR 60.4(a)]

None. None. Submit a r

schedule , USEPA RSubmit infDirector, ADivisionUSEPA, R290 BroadNew York60.4(a)]

Page 28 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

37 The owner or operator subject to the

provisions of 40 CFR Part 60 shall furnishthe Administrator written notification of anyphysical or operational change to an existingfacility which may increase the emission rateof any air pollutant to which a standardapplies, unless that change is specificallyexempted under an applicable subpart or inSec. 60.14(e). The notification shall includeinformation describing the precise nature ofthe change, present and proposed emissioncontrol systems, productive capacity offacility before and after the change and theexpected completion date of the change.Notification shall be postmarked within 60days or soon as practicable before anychange is commenced. The Administratormay request additional relevant informationsubsequent to this notice. [40 CFR60.7(a)(4)]

None. None. Submit no

event , notSouthern RCFR 60.7(

38 Annual emission limit based on operating

permit application, per boiler. Polycyclicorganic matter <= 0.11 tons/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

39 The owner or operator shall maintain a file

of all measurements, including continuousmonitoring system, monitoring device andperformance testing measurements; allcontinuous monitoring system performanceevaluations; all continuous monitoringsystem or monitoring device calibrationchecks; adjustments and maintenanceperformed on these systems or devices; andall other information required by this partrecorded in a permanent form suitable forinspection. [40 CFR 60.7(f)]

None. Other: See Applicable Requirement.[40

CFR 60.7(f)].

None.

Page 29 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

40 The owner or operator shall maintain

records of the occurence and duration of anystartup, shutdown, or malfunction in theoperation of an affected facility, anymalfunction of air pollution controlequipment or any periods during whichcontinuous monitoring system or monitoringdevice is inoperative. [40 CFR 60.7(b)]

None. Recordkeeping by manual logging of

parameter upon occurrence of event(permanently bound). [40 CFR 60.7(b)]

None.

41 At all times, including periods of startup,

shutdown and malfunctions, owners andoperators shall, to the extent practicable,maintain and operate any affected facilityincluding associated air pollution controlequipment in a manner consistent with goodair pollution control practice for minimizingemissions.Determination of whether acceptableoperating and maintenance procedures arebeing used will be based on informationavailable to the Administrator which mayinclude, but is not limited to, monitoringresults, opacity observations, review ofoperation and maintenance procedures, andinspection of the source. [40 CFR 60.11(d)]

None. None. None.

42 The NSPS opacity standard shall apply at all

times except during periods of start-up,shutdown, malfunctions, and as otherwisespecified in this permit. [40 CFR 60.11(c)]

None. None. None.

Page 30 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

43 The owner or operator shall develop a

QA/QC plan for all CEMS/COMS requiredby this permit. This QA/QC plan shallincorporate at a minimum those proceduresoutlined in 40 CFR, Part 60, Appendix Fand/or 40 CFR, Part 75, Appendix B forCEMS and those procedures outlined in 40CFR, Part 60, Appendix B, SpecificationOne and 40 CFR, Part 51, Proposed RM203 for COMS, published DepartmentTechnical Manuals or other proceduresapproved in writing by the Department. TheQA/QC plan shall designate a coordinatorfor the facility who is responsible to ensurethat the QA/QC plan is implemented. TheDepartment reserves the right to require theQA/QC plan to be revised at any time basedon the results of quarterly EEMPR reviews,inspections, audits or any other informationavailable to the Department. All proceduresoutlined in the QA/QC plan shall commenceupon the completion date of the PST. Allredundant CEMS/COMS must undergo theQA/QC procedure. [N.J.A.C. 7:27-22.16(a)]

Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis.[N.J.A.C. 7:27-22.16(o)].

Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports.[N.J.A.C. 7:27-22.16(o)].

Submit a rOctober 3preceding begin on JOctober 1NJDEP onquarterly aincluded ikept on filbe made arequest. [N

44 The permittee shall comply with all of the

requirements of Clean Air Interstate Rule(CAIR) permit for the CAIR NOX AnnualTrading Program, CAIR NOX OzoneSeason Trading Program, and CAIR SO2Trading Program issued for these affectedunits. [40 CFR 97]

Other: See attached CAIR Permit[40 CFR 97].

Other: See attached CAIR Permit[40 CFR 97].

Other (proattached C

45 For equipment subject to Compliance

Assurance Monitoring (CAM), perform themonitoring submitted per 40 CFR 64.3 [40CFR 64.3]

Other: Monitor the indicators per thesubmitted monitoring approach.[40 CFR64.6(c)(1)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem continuously. [40 CFR 64.9(b)]

Comply woccurrence 

Page 31 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

46 No owner or operator subject to NSPS

standards in Part 60, shall build, erect,install, or use any article, machine,equipment or process, the use of whichconceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to theatmosphere.[40 CFR 60.12]

None. None. None.

Page 32 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

47 Adjust the combustion process in

accordance with N.J.A.C.7:27-19.16 by May1 of each calendar year or within seven daysof the period of operation after May 1, if notoperated between January 1 and May 1 ofthat year. Record NOx and CO conc. aftereach adjustment and the O2 conc. at whichNOx and CO were measured. [N.J.A.C.7:27-19.4(c)] [N.J.A.C. 7:27-16.8(c)]

Monitored by continuous emissionmonitoring system continuously, based onan instantaneous determination. [N.J.A.C.7:27-16.8(c)]

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem annually in a permanently boundlogbook or readily accessible computermemory containing the followinginformation for each adjustment:1. The date of the adjustment and the timesat which it began and ended;2. The name, title and affiliation of theperson who made the adjustment;3. The NOx and CO concentration in theeffluent stream, in ppmvd, before and aftereach adjustment was made;4. The concentration of O2 (in percent drybasis) at which the CO and NOxconcentrations were measured pursuant tothe steps 3 a above;5. A description of any corrective actiontaken;6. Results from any subsequent testsperformed after taking any corrective action,including concentrations and convertedemission values in pounds per million BTU(lb/MMBtu);7. The type and amount of fuel used overthe 12 months prior to the annualadjustment; and8. Any other information which theDepartment or EPA has required as acondition of approval of any permit orcertificate issued for the equipment orsource operation. [N.J.A.C. 7:27-19.16]

Submit a r1/1/2009, that an annprocess rethe Departcombustioreport shainformatio1. The coneffluent stdry basis, adjustmen2. The conlb/MMBTbefore and combustio3. A descrtaken as pand4. The typover the 1adjustmen[N.J.A.C. 

Page 33 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

48 Except for system breakdowns, repairs,

calibration checks, and zero and spanadjustments, all continuous opacitymonitoring systems shall be in continuousoperation. They shall complete a minimumof one cycle of sampling and analyzing foreach successive 10-second period and onecycle of data recording for each successive6-minute period. [40 CFR 60.13(e)(1)]

Other: See Applicable Requirement. [40CFR 60.13(e)(1)].

Other: See Applicable Requirement. [40CFR 60.13(e)(1)].

None.

49 All continuous monitoring systems or

monitoring devices shall be installed suchthat representative measurements ofemissions or process parameters from theaffected facility are obtained. Proceduresfor location of continuous monitoringsytems contained in the applicablePerformance Specifications of Appendix Bof 40 CFR Part 60 shall be used.[40 CFR60.13(f)]

None. None. None.

Page 34 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

50 Mercury Emissions <= 3 milligrams per

MW-hr.On and after December 15, 2007, theemissions of mercury from Boiler #2 shallnot exceed 3.00 milligram per megawatt ofnet electricity generation, based on anannual weighted average of all valid stackemission tests performed for fourconsecutive quarters weighted by megawatthours produced each quarter.The annual weighted average mercuryemissions shall be calculated in accordancewith the formula specified in the definitionof "annual weighted average" set forth atN.J.A.C. 7:27-27.1.ORIn lieu of complying with the above, on andafter December 15, 2007, the permittee maycomply with the following requirement:The reduction efficiency for control ofmercury emissions of the air pollutioncontrol apparatus for control of mercuryshall be at least 90 percent based on theannual weighted average of all valid stackemission tests performed for fourconsecutive quarters weighted by megawatthours produced each quarter.The annual weighted average mercuryreduction efficiency shall be calculated inaccordance with the formula specified in thedefinition of "annual weighted average" setforth at N.J.A.C. 7:27-27.1. [N.J.A.C.7:27-27.27(a)]

Mercury Emissions: Monitored by stackemission testing quarterly: once per quarter;quarters shall begin on January 1, April 1,July 1, and October 1 of each year.On and after December 15, 2007, thepermittee shall conduct stack emissiontesting every quarter to measure mercury inthe gas stream in the stack in accordancewith a stack test protocol approved by theDepartment.The stack emission test shall be conducted atthe inlet of the air pollution controlapparatus and simultaneously at the exit ofthe air pollution control apparatus tomeasure the mass emission if the secondoption of reduction efficiency requirement isadopted.If the permittee achieves and maintainscompliance for eight consecutive quartersfor all applicable coal-fired boilers locatedat the facility, the permittee may reduce thefrequency of stack emission testing fromeach quarter to stack emission testingperformed every fourth quarter after theeighth quarter test in which annual weightedaverage compliance was determined.However, if annual stack emission testingfails to demonstrate compliance, then thefrequency of stack emission testing shallrevert to that indicated above.[N.J.A.C.7:27-27.7(a)1] and. [N.J.A.C.7:27-27.8]

Mercury Emissions: Recordkeeping by stacktest results quarterly: once per quarter;quarters shall begin on January 1, April 1,July 1, and October 1 of each year.If the permittee achieves and maintainscompliance for eight consecutive quartersfor all applicable coal-fired boilers locatedat the facility, the permittee may reduce thefrequency of stack emission testing fromeach quarter to stack emission testingperformed every fourth quarter after theeighth quarter test in which annual weightedaverage compliance was determined.However, if annual stack emission testingfails to demonstrate compliance, then thefrequency of stack emission testing shallrevert to that indicated above. [N.J.A.C.7:27-27.9]

Stack Test and submischedule. Bureau of Box 437, Tcalendar dquarter staThere shalruns per qbetween thpreceding be submittdays after to N.J.A.Cthe regionoffice and certified bor certified If the permcompliancfor all appat the facilfrequency each quartperformed eighth quaaverage coHowever, fails to demfrequency revert to thA summarsubmitted application expiration results shamegawatt [N.J.A.C. 7:27-22.18

Page 35 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

51 For equipment subject to Clean Air

Interstate Rule (CAIR) NOx TradingProgram, comply with N.J.A.C. 7:27-30.[N.J.A.C. 7:27-30]

Other: See N.J.A.C. 7:27-30. [N.J.A.C.7:27-30].

Other: See N.J.A.C. 7:27-30. [N.J.A.C.7:27-30].

Comply woccurrence 

52 The owner or operator shall reduce all

continuous monitoring systems (other thanopacity) data to 1-hour averages which shallbe computed from four or more data pointsequally spaced over each 1-hour period.Data recorded during periods of continuousmonitoring system breakdowns, repairs,calibraton checks, and zero and spanadjustments shall not be included in the dataaverages computed under this paragraph.For owners and operators complying withthe requirements in 40 CFR 60.7(f)(1) or(2), data averages must include any datarecorded during periods of monitorbreakdown or malfunction.An arithmetic or integrated average of alldata may be used. The data may berecorded in reduced or nonreduced form(e.g., ppm pollutant and percent O2 or ng/Jof pollutant).All exceedances shall be converted intounits of the standard using the applicableconversion procedures specified in subparts.After conversion into units of standard, thedata may be rounded to the same number ofsignificant digits as used in the applicablesubparts to specify the emission limit (e.g.rounded to the nearest 1 percent opacity).[40 CFR 60.13(h)]

None. Other: See Applicable Requirement.[40

CFR 60.13(h)].

None.

53 The owner or operator shall perform zero

and span adjustments daily for continuousemission monitors and continuous opacitymonitors following procedures outlined in40 CFR Part 60.13(d)1 & 2. [40 CFR60.13(d)]

None. Other: Maintain records in accordance with

40 CFR 60.7(f). [40 CFR 60.13(d)].

None.

Page 36 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

54 Except for system breakdowns, repairs,

calibration checks, and zero and spanadjustments, all continuous monitoringsystems measuring emissions except opacityshall be in continuous operation. They shallcomplete a minimum of one cycle ofoperation (sampling, analyzing and datarecording) for each successive 15-minuteperiod. [40 CFR 60.13(e)(2)]

Other: See Applicable Requirement. [40CFR 60.13(e)(2)].

Other: See Applicable Requirement. [40CFR 60.13(e)(2)].

None.

55 The owner or operator shall reduce all

continuous monitoring systems formeasuring opacity data to 6-minute averageswhich shall be calculated from 36 or moredata points equally spaced over each6-minute period. Data recorded duringperiods of continuous monitoring systembreakdowns, repairs, calibration checks, andzero and span adjustments shall not beincluded in the data averages computedunder this paragraph. For owners andoperators complying with the requirementsin 40 CFR 60.7(f)(1) or (2), data averagesmust include any data recorded duringperiods of monitor breakdown ormalfunction. An arithmetic or integratedaverage of all data may be used. The datamay be recorded in reduced or nonreducedform (e.g., ppm pollutant and percent O2 orng of pollutant per J of heat input). Allexcess emissions shall be converted intounits of the standard using the applicableconversion procedures specified in subparts.After conversion into units of the standard,the data may be rounded to the same numberof significant digits as used in the applicablesubparts to specify the emission limit (e.g.rounded to the nearest 1 percent opacity).[40 CFR 60.13(h)]

Monitored by continuous opacitymonitoring system at no required frequency,based on 6 minute blocks. [40 CFR60.11(b)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [40 CFR 60.11(b)]

None.

Page 37 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

56 The owner or operator shall develop a

QA/QC plan for each CEMS/COMSrequired by this permit prepared inaccordance with the NJDEP TechnicalManual 1005 posted on the AQPP webpageat http://www.state.nj.us/dep/aqpp.[N.J.A.C. 7:27-22.16(a)]

Other: The QA/QC coordinator shall beresponsible for reviewing the QA/QC planon an annual basis. [N.J.A.C.7:27-22.16(o)].

Other: Maintain readily accessible recordsof the QA/QC plan including QA date andquarterly reports. [N.J.A.C. 7:27-22.16(o)].

None.

57 Periodic emission monitoring for NOx, CO,

VOC and O2 shall be consistent with therequirements specified in NJDEP TechnicalManual 1005 posted on AQPP webpage athttp://www.state.nj.us/dep/aqpp. Thepermittee shall use reference method or sitespecific method testing provided in theTechnical Manual 1005 as part of anyperiodic monitoring procedure. [N.J.A.C.7:27-22.16(a)]

None. None. None.

Page 38 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

58 NOx (Total) <= 2.8 lb/MW-hr When

combusting #6 fuel oil or # 2 fuel oil.This limit will become operative onDecember 15, 2012. [N.J.A.C. 7:27-19.4(a)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) averageCalculated as the combined total Ib/hremissions divided by the total sum of theMWh to PJM grid, MWh to the host, anduseful steam to the host. Per N.J.A.C.7:27-19.4(e), excludes emissions when theplant is not supplying MWh to PJM grid.Carney's Point Generating Plant intends tocalculate the useful heat input per N.J.A.C.7:27-19.4(f) using this equation:MWh = Metered Steam to Host (Ib) * 1,125Btu/lb * 2.93E-7 Btu/MWhwhere:1,125 Btu/lb = process steam energy (1,200Btu/lb) - ambient water energy (75 Btu/lb)2.93E-7 Btu/MWh = numerical conversionfactorWhen calculating a 24-hour NOx emissionrate for an affected coal-fired unit, the owneror operator may exclude emissions from: A unit that has ceased firing fossil fuel, theperiod of time, not to exceed six hours, frominitial firing of the unit until the unit is firedwith coal and synchronized with a utilityelectric distribution system; andThe six hour start-up exemption from thecalculation of 24-hour average emission rateapplies to the determination of the outputbased NOx factor estimated in units oflb/MW-hr. [N.J.A.C. 7:27-19.4(e)]&.[N.J.A.C. 7:27-19.15(a)1]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-19.19(a)]

Submit an Monitorin(EEMPR)30, Octobepreceding quarters beand OctobNJDEP on[N.J.A.C. 

Page 39 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

59 NOx (Total) <= 1.5 lb/MW-hr when

combusting coal, with or without #6 fuel oilor #2 fuel oil. This limit will becomeoperative on December 15, 2012. [N.J.A.C.7:27-19.4(a)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) averageCalculated as the combined total Ib/hremissions divided by the total sum of theMWh to PJM grid, MWh to the host, anduseful steam to the host. Per N.J.A.C.7:27-19.4(e), excludes emissions when theplant is not supplying MWh to PJM grid.Carney's Point Generating Plant intends tocalculate the useful heat input per N.J.A.C.7:27-19.4(f) using this equation:MWh = Metered Steam to Host (Ib) * 1,125Btu/lb * 2.93E-7 Btu/MWhwhere:1,125 Btu/lb = process steam energy (1,200Btu/lb) - ambient water energy (75 Btu/lb)2.93E-7 Btu/MWh = numerical conversionfactorWhen calculating a 24-hour NOx emissionrate for an affected coal-fired unit, the owneror operator may exclude emissions from: A unit that has ceased firing fossil fuel, theperiod of time, not to exceed six hours, frominitial firing of the unit until the unit is firedwith coal and synchronized with a utilityelectric distribution system; andThe six hour start-up exemption from thecalculation of 24-hour average emission rateapplies to the determination of the outputbased NOx factor estimated in units oflb/MW-hr. [N.J.A.C. 7:27-19.4(e)]&.[N.J.A.C. 7:27-19.15(a)1]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-19.19(a)]

Submit an Monitorin(EEMPR)30, Octobepreceding quarters beand OctobNJDEP on[N.J.A.C. 

Page 40 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

60 NOx (Total) <= 1 lb/MW-hr when

combusting #2 fuel oil. This limit willbecome operative on May 1, 2015.[N.J.A.C. 7:27-19.4(a)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a calendar day (in ozone season) or30 day rolling (at other times) averageCalculated as the combined total Ib/hremissions divided by the total sum of theMWh to PJM grid, MWh to the host, anduseful steam to the host. Per N.J.A.C.7:27-19.4(e), excludes emissions when theplant is not supplying MWh to PJM grid.Carney's Point Generating Plant intends tocalculate the useful heat input per N.J.A.C.7:27-19.4(f) using this equation:MWh = Metered Steam to Host (Ib) * 1,125Btu/lb * 2.93E-7 Btu/MWhwhere:1,125 Btu/lb = process steam energy (1,200Btu/lb) - ambient water energy (75 Btu/lb)2.93E-7 Btu/MWh = numerical conversionfactorWhen calculating a 24-hour NOx emissionrate for an affected coal-fired unit, the owneror operator may exclude emissions from: A unit that has ceased firing fossil fuel, theperiod of time, not to exceed six hours, frominitial firing of the unit until the unit is firedwith coal and synchronized with a utilityelectric distribution system; andThe six hour start-up exemption from thecalculation of 24-hour average emission rateapplies to the determination of the outputbased NOx factor estimated in units oflb/MW-hr. [N.J.A.C. 7:27-19.4(e)]&.[N.J.A.C. 7:27-19.15(a)1]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-19.19(a)]

Submit an Monitorin(EEMPR)30, Octobepreceding begin on JOctober 1NJDEP on[N.J.A.C. 

Page 41 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

61 THE PERMITTEE SHALL SUBMIT AN

APPLICATION FOR A SIGNIFICANTMODIFICATION PURSUANT TON.J.A.C. 7:27-22.24, BY DECEMBER 31,2014, TO INCLUDE THE APPLICABLECONDITIONS OF 40 CFR 63, SUBPARTA (GENERAL PROVISIONS) ANDSUBPART UUUUU (NATIONALEMISSION STANDARDS FORHAZARDOUS AIR POLLUTANTS: COALAND OIL FIRED ELECTRIC UTILITYSTEAM GENERATING UNITS.) THECOMPLIANCE DATE FOR 40 CFR 63SUBPART UUUUU IS APRIL 15, 2015.[N.J.A.C. 7:27-22.16(a)]

None. None. Other (pro

THE OPESIGNIFICAPPLICA[N.J.A.C. 

Page 42 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: GR2 PC Boilers #1 & #2, Normal firing using coal, No. 6 and/or No. 2 oil

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 All air pollution control apparatus must be

operating when coal and/or No. 6 fuel oil isburning. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 Sulfur Content in Fuel <= 0.3 % by weight

for No. 6 fuel oil, based on preconstructionpermit. [N.J.A.C. 7:27-22.16(e)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

3 Nitrogen oxides emissions from the PC

boiler shall be controlled by low NOxburners, advanced combustion controls, andselective catalytic reduction (SCR)technology. [N.J.A.C. 7:27-22.16(e)]

Monitored by continuous emissionmonitoring system continuously. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

None.

4 Sulfur Content in Fuel <= 500 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective through June30, 2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

5 Sulfur Content in Fuel <= 15 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective from July 1,2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

6 Sulfur Content in Fuel <= 5,000 ppmw.

Maximum allowable sulfur content in #6fuel oil by fuel oil type/viscosity andgeographical zone. [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

7 SO2 <= 0.25 lb/MMBTU on and after

December 15, 2012, based on a 24 houraverage for every calendar day. [N.J.A.C.7:27-10.2(h)]

SO2: Monitored by continuous emissionmonitoring system continuously, based onone calendar day based on each valid hourblock average over every day the facilityoperates the pulverized coal boiler andburns bituminous coal. Startup andshutdown emissions shall be excluded asdefined at N.J.A.C. 7:27-10.5(c). [N.J.A.C.7:27-10.5(b)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storage eachhour during operation. [N.J.A.C.7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, Octobepreceding begin on JOctober 1NJDEP on[N.J.A.C. 

Page 43 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Sulfur dioxide emissions from the PC boiler

shall be controlled by lime spray dryerabsorber scrubbers, except when burningonly No. 2 fuel oil. [N.J.A.C. 7:27-22.16(e)]

Monitored by continuous emissionmonitoring system continuously. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

None.

9 Sulfur Content in Fuel <= 2 % by weight.

Based on preconstruction permit, maximumallowable sulfur content of bituminous coal<= 2 percent by weight based on acomposite sample of all shipments in acalendar month. [N.J.A.C. 7:27-22.16(e)]

Sulfur Content in Fuel: Monitored by fuelsampling (e.g. coal) once per bulk fuelshipment , based on composite sample of allcoal shipments in one calendar month on aweighted average basis. [N.J.A.C.7:27-22.16(o)]

Other: Keep Certificate of Analysis showingfuel sulfur content, per delivery.[N.J.A.C.7:27-22.16(o)].

None.

10 Maximum emission rate based on

preconstruction permit. PM-10 (Total) <=0.018 lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

PM-10 (Total): Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runs.(See Applicable Requirement for GR1PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

11 Maximum emission rate from

preconstruction permit, per boiler. VOC(Total) <= 5 lb/hr. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

14 Maximum emission rate from

preconstruction permit, per boiler. PM-10(Total) <= 25 lb/hr. [N.J.A.C.7:27-22.16(e)]

PM-10 (Total): Monitored by stack emissiontesting annually, based on the average ofthree Department validated stack test runs.(See Applicable Requirement for GR1PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

Page 44 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

13 Particulate emissions from the PC boiler

shall be controlled by baghouse. Baghousesmay only be bypassed when firing only No.2 fuel oil in the boiler and during plantshutdowns resulting from conditions thatcould damage the baghouse. In case ofbypass of a baghouse, the coal feed to theboiler shall be tripped as specified by themanufacturer's emergency shutdownstandard operating procedure. Thebaghouse bypass dampers shall be designedto open on loss of supply air and loss ofpower to the solenoids. For any otherreasons, no exception is provided from theemission limits specified in this permit.Baghouses shall be provided with adequateaccess for inspection. [N.J.A.C.7:27-22.16(e)]

Other: Monitored by differential pressuretransmitter, continuously. The permitteeshall install, calibrate and maintain themonitor(s) in accordance with themanufacturer's specifications.[N.J.A.C.7:27-22.16(o)].

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. Record pressure drop acrossentire fabric filter. [N.J.A.C. 7:27-22.16(o)]

None.

12 SO2 <= 0.15 lb/MMBTU on and after

December 15, 2012, based on a 30 calendarday rolling average determined inaccordance with N.J.A.C. 7:27-10.5.[N.J.A.C. 7:27-10.2(h)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on arolling 30 day average (rolling 1 day basis)Any calendar day during which nocombustion of solid fuel occurred shall notbe included in the 30-calendar day rollingaverage emission rate. Startup andshutdown emissions shall be excluded asdefined at N.J.A.C. 7:27-10.5(c). [N.J.A.C.7:27-10.5(b)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, Octobepreceding begin on JOctober 1NJDEP on[N.J.A.C. 

17 Maximum concentration value from

preconstruction permit. CO <= 100 ppmdv@ 7% O2. [N.J.A.C. 7:27-22.16(e)]

CO: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average and stack emission testingbased on the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously and stack test results. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

16 Opacity <= 10 %. At all times, with the

exception of start-up and shutdown, visibleemissions from the PC boiler shall notexceed 10% opacity except for a period notlonger than three minutes in any consecutive30-minute period. [N.J.A.C. 7:27-22.16(e)]

Opacity: Monitored by continuous opacitymonitoring system continuously, based onany consecutive 30-minute period. [N.J.A.C.7:27-22.16(o)]

Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

None.

Page 45 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

15 Maximum emission rate. PM-2.5 (Total) <=

0.018 lb/MMBTU. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

18 Maximum concentration value from

preconstruction permit. SO2 <= 100 ppmdv@ 7% O2. [N.J.A.C. 7:27-22.16(e)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on a3 hour rolling average based on a 1 hourblock average and stack emission testingbased on the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously and stack test results. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

19 Maximum emission rate per boiler, PM-2.5

(Total) <= 25 lb/hr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

20 Maximum emission rate based on

preconstruction permit, per boiler. CO <=152.8 lb/hr. [N.J.A.C. 7:27-22.16(e)]

CO: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. (See Applicable Requirement forGR1 PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

21 Maximum emission rate based on

preconstruction permit. TSP <= 0.018lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

TSP: Monitored by stack emission testingannually, based on the average of threeDepartment validated stack test runs. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

TSP: Recordkeeping by stack test resultsannually (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

22 Maximum emission rate based on operating

permit application, per boiler. Hydrogenchloride <= 10.4 lb/hr. [N.J.A.C.7:27-22.16(a)]

Hydrogen chloride: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Hydrogen chloride: Recordkeeping by stacktest results annually (See ApplicableRequirement for GR1 PCBoilSUMReference #3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

23 Maximum emission rate from

preconstruction permit. VOC (Total) <=0.0036 lb/MMBTU. [N.J.A.C.7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

Page 46 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

24 TSP <= 25 lb/hr Maximum emission rate

from preconstruction permit, per boiler.[N.J.A.C. 7:27-22.16(e)]

TSP: Monitored by stack emission testingannually, based on the average of threeDepartment validated stack test runs. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 3) . [N.J.A.C.7:27-22.16(o)]

TSP: Recordkeeping by stack test resultsannually (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

25 Maximum emission rate from

preconstruction permit, per boiler.Beryllium Emissions <= 0.0058 lb/hr.[N.J.A.C. 7:27-22.16(e)]

Beryllium Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Beryllium Emissions: Recordkeeping bystack test results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

26 Maximum emission rate from

preconstruction permit, per boiler. SO2 <=305.6 lb/hr. [N.J.A.C. 7:27-22.16(e)]

SO2: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. (See Applicable Requirement forGR1 PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

SO2: Recordkeeping by stack test resultsprior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

27 Maximum emission rate from

preconstruction permit, per boiler. TotalChromium Emissions <= 0.051 lb/hr.[N.J.A.C. 7:27-22.16(e)]

Chromium Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Chromium Emissions: Recordkeeping bystack test results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

28 Maximum concentration value from

preconstruction permit. VOC (Total) <= 7ppmdv @ 7% O2. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

29 Maximum emission rate from

preconstruction permit, per boiler. NOx(Total) <= 208.5 lb/hr. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults prior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

Page 47 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

30 Maximum concentration value from

preconstruction permit. NOx (Total) <= 90ppmdv @ 7% O2. [N.J.A.C. 7:27-22.16(e)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a 3 hour rolling average based on a1 hour block average and stack emissiontesting based on the average of threeDepartment validated stack test runs. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously and stack test results.(See Applicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

31 Maximum emission rate based on operating

permit application, per boiler. Seleniumcompounds <= 0.72 lb/hr. [N.J.A.C.7:27-22.16(a)]

Selenium compounds: Monitored by stackemission testing prior to permit expirationdate, based on the average of threeDepartment validated stack test runs (SeeApplicable Requirement for GR1PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Selenium compounds: Recordkeeping bystack test results prior to permit expirationdate (See Applicable Requirement for GR1PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

32 Maximum emission rate based on

preconstruction permit. CO <= 0.11lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

CO: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. (See Applicable Requirement forGR1 PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

33 Maximum emission rate from

preconstruction permit, per boiler. FluoridesEmissions (as HF) <= 2.78 lb/hr. [N.J.A.C.7:27-22.16(e)]

Fluorides Emissions (as HF): Monitored bystack emission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Fluorides Emissions (as HF):Recordkeeping by stack test results annually(See Applicable Requirement for GR1PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

34 NOx (Total) <= 0.15 lb/MMBTU.

Maximum emission rate based onpreconstruction permit. [N.J.A.C.7:27-22.16(e)]

NOx (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults prior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

35 Maximum emission rate based on operating

permit application, per boiler. Formaldehyde<= 0.308 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 48 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

36 Ammonia <= 5 ppmvd @ 7% O2 based on a

30 day rolling average (rolling one-daybasis). Maximum concentration value frompreconstruction permit. [N.J.A.C.7:27-22.16(a)]

Ammonia: Monitored by continuousemission monitor continuously, based on a30 day rolling average (rolling one-daybasis). [N.J.A.C. 7:27-22.16(e)]

None. None.

37 Maximum emission rate based on

preconstruction permit. SO2 <= 0.22lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

SO2: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. (See Applicable Requirement forGR1 PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

SO2: Recordkeeping by stack test resultsprior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

38 Maximum concentration value from

preconstruction permit. Ammonia <= 10ppmvd @ 7% O2. [N.J.A.C. 7:27-22.16(a)]

Ammonia: Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

Ammonia: Recordkeeping by stack testresults prior to permit expiration date. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

39 Maximum emission rate based on operating

permit application, per boiler. Nickelcompounds <= 1.2 lb/hr. [N.J.A.C.7:27-22.16(a)]

Nickel compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Nickel compounds: Recordkeeping by stacktest results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

40 Maximum emission rate from

preconstruction permit, per boiler. Ammonia<= 10 lb/hr. [N.J.A.C. 7:27-22.16(a)]

Ammonia: Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

Ammonia: Recordkeeping by stack testresults prior to permit expiration date. (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

41 Maximum emission rate based on operating

permit application, per boiler. Phosphorus<= 3.2 lb/hr. [N.J.A.C. 7:27-22.16(a)]

Phosphorus: Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

Phosphorus: Recordkeeping by stack testresults prior to permit expiration date (SeeApplicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

Page 49 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

42 Ammonia process monitors shall be

maintained and operated as a tool to monitorthe ammonia slip level. Alarm setpoint shallbe set at 10 ppmdv @ 7% O2. Note:Ammonia monitors shall not be used todetermine compliance with the ammoniapermit limit. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by process monitorcontinuously, based on a 3 hour rollingaverage based on a 1 hour blockaverage.[N.J.A.C. 7:27-22.16(o)].

Other: Data acquisition system (DAS) orelectronic data storage continuously, basedon a 1 hour block average.[N.J.A.C.7:27-22.16(o)].

None.

43 Maximum emission rate based on operating

permit application, per boiler. Polycyclicorganic matter <= 0.025 lb/hr. [N.J.A.C.7:27-22.16(a)]

Polycyclic organic matter: Monitored bystack emission testing prior to permitexpiration date, based on the average ofthree Department validated stack test runs(See Applicable Requirement for GR1PCBoilSUM Reference # 2). [N.J.A.C.7:27-22.16(o)]

Polycyclic organic matter: Recordkeepingby stack test results prior to permitexpiration date (See ApplicableRequirement for GR1 PCBoilSUMReference # 2). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

44 Ammonia process monitors shall be

maintained and operated as a tool to monitorthe ammonia slip level. Alarm setpoint shallbe set at 5 ppmdv @ 7% O2. Note:Ammonia monitors shall not be used todetermine compliance with the ammoniapermit limit. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by process monitorcontinuously, based on a 30 day rollingaverage (rolling 1 day basis).[N.J.A.C.7:27-22.16(o)].

Other: Data acquisition system (DAS) orelectronic data storage continuously, basedon a one day basis.[N.J.A.C. 7:27-22.16(o)].

None.

45 Ammonia process monitors shall be

maintained and operated as a tool to monitorthe ammonia slip level. Alarm setpoint shallbe set at 10 lb/hr. Note: Ammonia monitorsshall not be used to determine compliancewith the ammonia permit limit. [N.J.A.C.7:27-22.16(a)]

Other: Monitored by process monitorcontinuously, based on a 3 hour rollingaverage based on a 1 hour blockaverage.[N.J.A.C. 7:27-22.16(o)].

Other: Data acquisition system (DAS) orelectronic data storage continuously, basedon a 3 hour rolling average based on a 1hour block average.[N.J.A.C.7:27-22.16(o)].

None.

46 Maximum emission rate based on operating

permit application, per boiler. Cobaltcompounds <= 0.19 lb/hr. [N.J.A.C.7:27-22.16(a)]

Cobalt compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Cobalt compounds: Recordkeeping by stacktest results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

47 Maximum emission rate from

preconstruction permit, per boiler. ArsenicEmissions <= 0.117 lb/hr. [N.J.A.C.7:27-22.16(e)]

Arsenic Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Arsenic Emissions: Recordkeeping by stacktest results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

Page 50 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

48 The owner or operator shall install and

operate a continuous monitoring system formeasuring the oxygen content of the fluegases at each location where sulfur dioxideor nitrogen oxides emissions are monitored.[40 CFR 60.49Da(d)]

Monitored by continuous emissionmonitoring system continuously, based on arolling 30 day average (rolling 1 day basis).[40 CFR 60.49Da(d)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [40 CFR 60.49Da(a)]

Submit a rschedule. submit to from the inperformanCFR 60.5

49 Maximum emission rate from

preconstruction permit, per boiler. CadmiumEmissions <= 0.003 lb/hr. [N.J.A.C.7:27-22.16(e)]

Cadmium Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Cadmium Emissions: Recordkeeping bystack test results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

50 Maximum emission rate from

preconstruction permit, per boiler. LeadEmissions <= 0.04 lb/hr. [N.J.A.C.7:27-22.16(e)]

Lead Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Lead Emissions: Recordkeeping by stacktest results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

51 Maximum emission rate based on operating

permit application, per boiler. Manganesecompounds <= 1.5 lb/hr. [N.J.A.C.7:27-22.16(a)]

Manganese compounds: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Manganese compounds: Recordkeeping bystack test results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

52 Mercury Emissions <= 0.0015 lb/hr , per

boiler. [N.J.A.C. 7:27-22.16(a)]

Mercury Emissions: Monitored by stackemission testing annually, based on theaverage of three Department validated stacktest runs (See Applicable Requirement forGR1 PCBoilSUM Reference # 3). [N.J.A.C.7:27-22.16(o)]

Mercury Emissions: Recordkeeping by stacktest results annually (See ApplicableRequirement for GR1 PCBoilSUMReference # 3). [N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule (GR1 PCB7:27-22.16

Page 51 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

53 The owner or operator shall submit written

reports to the Administrator, all informationspecified at 40 CFR 60.51a(b), (c), (d), (f),(g), and (h). See Attachment #1. [40 CFR60.51Da(j)]

Other: See Attachment #1.[40 CFR60.51Da(j)].

Other: See Attachment #1.[40 CFR60.51Da(j)].

Submit a rschedule. day followperiod. Thinformatiothrough (hbe accompprepared aThe report Region II Regional Osemiannuathe 30th dreporting pCFR 60.4

54 The owner or operator of an affected facility

may submit electronic quarterly reports forSO2 and/or NOx and/or opacity in lieu ofsubmitting written reports required under 40CFR 60.51a(b) & 40 CFR 60.51a(i). [40CFR 60.51Da(k)]

None. None. Submit a r

schedule. submitted of the caleaccompanfrom the owhether coemission srequiremeduring the Before subformat, the coordinate obtain theithis alternquarterly ecoordinate[40 CFR 

Page 52 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

55 NOx (Total): When combusting coal and/or

No. 2 fuel oil, NOx emissions shall notexceed the limit as calculated by thefollowing equation:En = (0.3x + 0.6y)/100,where En is the prorated nitrogen oxideslimit in lb/MMBtu; x is the percentage of total heat inputderived from #2 fuel oil; and y is the percentage of total heat inputderived from coal.This limit shall apply at all times exceptduring periods of start-up, shutdown, ormalfunction. [40 CFR 60.44Da(a)(1)]

NOx (Total): Monitored by continuousemission monitoring system continuously,based on a rolling 30 day average (rolling 1day basis). [40 CFR 60.49Da(d)]

NOx (Total): Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [40 CFR 60.51Da(b)]

Submit an Monitorin(EEMPR)and July 1 than three the approvinclude dathe reportiAttachmen

56 SO2 <= 0.15 lb/MMBTU. or SO2<=

1.20lb/MMBTU and 10 percent of potentialcombustion concentration, or SO2<=30percent of potential combustionconcentration when emissions are less than0.6 lb/MMBTU, or SO2<=1.4 lb/MW-hrgross energy output. [40 CFR 60.43Da(a)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on arolling 30 day average (rolling 1 day basis) .[40 CFR 60.43Da(g)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [40 CFR 60.49(Da)(b)]

Submit an Monitorin(EEMPR)30, Octobepreceding quarters beand OctobNJDEP onAttachmen

57 Particulate Emissions <= 0.03 lb/MMBTU.

This emission standard does not applyduring periods of startup, shutdown, ormalfunction. [40 CFR 60.42Da(a)]

Particulate Emissions: Monitored by stackemission testing annually, based on each ofthree Department validated stack test runs.In conducting the performance tests requiredin 40 CFR 60.8, the owner or operator shalluse the procedures specified at 40 CFR 60Appendix A to demonstrate compliance. Theowner or operator of an affected facility thathas not operated for 60 consecutive calendardays prior to the date that the subsequentperformance test would have been requiredhad the unit been operating is not requiredto perform the subsequent performance testuntil 30 calendar days after the next boileroperating day. [40 CFR 60.48(o)] &. [40CFR 60.50(Da)(b)(1)]

Particulate Emissions: Recordkeeping bystack test results annually. [40 CFR60.51(Da)(a)]

Submit a sstack testinsubmit resto the Admtesting. [4

Page 53 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

58 Opacity <= 20 % at all times, except one

6-minute period per hour of not more than27% opacity. This standard does not applyduring periods of start-up, shutdown, ormalfunction. [40 CFR 60.42Da(b)]

Opacity: Monitored by continuous opacitymonitoring system continuously, based on 6minute blocks. [40 CFR 60.47Da(a)]

Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [40 CFR 60.47Da(a)]

Submit an Monitorin(EEMPR)30, Octobepreceding quarters beand OctobNJDEP on[N.J.A.C. 

Page 54 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: GR3 PC Boilers #1 & #2, Start-up

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions greater than 20%

opacity, exclusive of condensed watervapor, except for a period of not longer thanthree minutes, in any consecutive 30-minuteperiod, during a period of PC boiler start-upand shutdown. [N.J.A.C. 7:27-22.16(e)]

Monitored by continuous opacitymonitoring system continuously, based onany consecutive 30-minute period. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

None.

2 Start-up is defined as the period of time

beginning with initial firing of #2 fuel oiland ending at the time the boiler is beingfired only with coal and/or #6 fuel oil. Nocoal or #6 fuel oil may be fired until all airpollution control apparatus is in operation.Start-up Period <= 6 hours. [N.J.A.C.7:27-22.16(e)]

Start-up Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Start-up Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]

None.

3 Sulfur Content in Fuel <= 500 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective through June30, 2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

4 Sulfur Content in Fuel <= 15 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective from July 1,2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

5 Sulfur Content in Fuel <= 5,000 ppmw.

Maximum allowable sulfur content in #6fuel oil by fuel oil type/viscosity andgeographical zone. [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

6 SO2 <= 0.25 lb/MMBTU on and after

December 15, 2012, based on a 24 houraverage for every calendar day. [N.J.A.C.7:27-10.2(h)]

SO2: Monitored by continuous emissionmonitoring system continuously, based onone calendar day based on each valid hourblock average over every day the facilityoperates the pulverized coal boiler andburns bituminous coal. Startup andshutdown emissions shall be excluded asdefined at N.J.A.C. 7:27-10.5(c). [N.J.A.C.7:27-10.5(b)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storage eachhour during operation. [N.J.A.C.7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, Octobepreceding begin on JOctober 1NJDEP on[N.J.A.C. 

Page 55 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 SO2 <= 0.15 lb/MMBTU on and after

December 15, 2012, based on a 30 calendarday rolling average determined inaccordance with N.J.A.C. 7:27-10.5.[N.J.A.C. 7:27-10.2(h)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on arolling 30 day average (rolling 1 day basis)Any calendar day during which nocombustion of solid fuel occurred shall notbe included in the 30-calendar day rollingaverage emission rate. Startup andshutdown emissions shall be excluded asdefined at N.J.A.C. 7:27-10.5(c). [N.J.A.C.7:27-10.5(b)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, Octobepreceding begin on JOctober 1NJDEP on[N.J.A.C. 

8 Sulfur Content in Fuel <= 2 % by weight.

Based on preconstruction permit, maximumallowable sulfur content of bituminous coal<= 2 percent by weight based on acomposite sample of all shipments in acalendar month. [N.J.A.C. 7:27-22.16(e)]

Sulfur Content in Fuel: Monitored by fuelsampling (e.g. coal) once per bulk fuelshipment , based on composite sample of allcoal shipments in one calendar month on aweighted average basis. [N.J.A.C.7:27-22.16(o)]

Other: Keep Certificate of Analysis showingfuel sulfur content, per delivery.[N.J.A.C.7:27-22.16(o)].

None.

Page 56 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: GR4 PC Boilers #1 & #2, Shut-Down

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions greater than 20%

opacity, exclusive of condensed watervapor, except for a period of not longer thanthree minutes, in any consecutive 30-minuteperiod, during a period of PC boiler start-upand shutdown. [N.J.A.C. 7:27-22.16(e)]

Monitored by continuous opacitymonitoring system continuously, based onany consecutive 30-minute period. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

None.

2 Sulfur Content in Fuel <= 500 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective through June30, 2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

3 Sulfur Content in Fuel <= 15 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective from July 1,2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

4 Sulfur Content in Fuel <= 5,000 ppmw.

Maximum allowable sulfur content in #6fuel oil by fuel oil type/viscosity andgeographical zone. [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

5 SO2 <= 0.25 lb/MMBTU on and after

December 15, 2012, based on a 24 houraverage for every calendar day. [N.J.A.C.7:27-10.2(h)]

SO2: Monitored by continuous emissionmonitoring system continuously, based onone calendar day based on each valid hourblock average over every day the facilityoperates the pulverized coal boiler andburns bituminous coal. Startup andshutdown emissions shall be excluded asdefined at N.J.A.C. 7:27-10.5(c). [N.J.A.C.7:27-10.5(b)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storage eachhour during operation. [N.J.A.C.7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, Octobepreceding begin on JOctober 1NJDEP on[N.J.A.C. 

6 Based on preconstruction permit, maximum

allowable sulfur content of No. 6 fuel oil,Sulfur Content in Fuel <= 0.3 % by weight.[N.J.A.C. 7:27-22.16(e)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

Page 57 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 Shutdown is defined as the period of time

beginning with the interruption of coal feedand ending when fuel is no longer beingintroduced into the combustion chamber ofthe boiler. All air pollution controlapparatus must be operating when coaland/or #6 fuel oil is burning. If theshutdown period exceeds one hour,compliance with emissions limits will bebased on uncorrected CEMs data, foroxygen in the utility boiler effluent, untilshutdown is completed. Shutdown Period <= 1 hours. [N.J.A.C.7:27-22.16(e)]

Shutdown Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Shutdown Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]

None.

8 SO2 <= 0.15 lb/MMBTU on and after

December 15, 2012, based on a 30 calendarday rolling average determined inaccordance with N.J.A.C. 7:27-10.5.[N.J.A.C. 7:27-10.2(h)]

SO2: Monitored by continuous emissionmonitoring system continuously, based on arolling 30 day average (rolling 1 day basis)Any calendar day during which nocombustion of solid fuel occurred shall notbe included in the 30-calendar day rollingaverage emission rate. Startup andshutdown emissions shall be excluded asdefined at N.J.A.C. 7:27-10.5(c). [N.J.A.C.7:27-10.5(b)]

SO2: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

Submit an Monitorin(EEMPR)30, Octobepreceding begin on JOctober 1NJDEP on[N.J.A.C. 

9 Sulfur Content in Fuel <= 2 % by weight.

Based on preconstruction permit, maximumallowable sulfur content of bituminous coal<= 2 percent by weight based on acomposite sample of all shipments in acalendar month. [N.J.A.C. 7:27-22.16(e)]

Sulfur Content in Fuel: Monitored by fuelsampling (e.g. coal) once per bulk fuelshipment , based on composite sample of allcoal shipments in one calendar month on aweighted average basis. [N.J.A.C.7:27-22.16(o)]

Other: Keep Certificate of Analysis showingfuel sulfur content, per delivery.[N.J.A.C.7:27-22.16(o)].

None.

Page 58 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Subject Item: GR5 U10, U11, U13, U14, U18

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 All requests, reports, applications,

submittals, and other communications to theAdministrator pursuant to Part 60 shall besubmitted in duplicate to the RegionalOffice of US Environmental ProtectionAgency. [40 CFR 60.4(a)]

None. None. Other (pro

approved Region II Submit ReAir and WEnvironmII, 290 Bro10007-186

2 Submit a copy of all requests, reports,

applications, submittals, and othercommunications required by 40 CFR Part 60to the Southern Regional EnforcementOffice of NJDEP. [40 CFR 60.4(b)]

None. None. Other (pro

approved Southern RCFR 60. TNJDEP, SOffice, OnSuite 201, 60.4(b)]

3 A notification of any physical or operational

change to an existing facility which mayincrease the emission rate of any airpollutant to which a standard applies, unlessthat change is specifically exempted underan applicable subpart or in section 60.14(e).This notice shall be postmarked 60 days oras soon as practicable before the change iscommenced and shall include informationdescribing the precise nature of the change,present and proposed emission controlsystems, productive capacity of the facilitybefore and after the change, and theexpected completion date of the change.The Administrator may request additionalrelevant information subsequent to thisnotice. [40 CFR 60.7(a)(4)]

None. None. Comply w

occurrence EPA RegiEnforcemeCFR 60.7(

Page 59 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

4 The owner or operator shall maintain

records of the occurrence and duration ofany startup, shutdown, or malfunction in theoperation of an affected facility, anymalfunction of air pollution controlequipment or any periods during whichcontinuous monitoring system or monitoringdevice is inoperative. [40 CFR 60.7(b)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. [40 CFR60.7(b)]

None.

5 Any owner or operator subject to the

provisions of this part shall maintain a fileof all measurements, including continuousmonitoring system, monitoring device andperformance testing measurements; allcontinuous monitoring system performanceevaluations; all continuous monitoringsystem or monitoring device calibrationchecks; adjustments and maintenanceperformed on these systems or devices ; andall other information required by this partrecorded in a permanent form suitable forinspection. [40 CFR 60.7(f)]

None. Other: See Applicable Requirement.[40

CFR 60.7(f)].

None.

6 The NSPS opacity standards shall apply at

all times except during periods of start-up,shutdown, malfunction, and as otherwiseprovided in 40 CFR Part 60. [40 CFR60.11(c)]

None. None. None.

7 At all times, including periods of startup,

shutdown and malfunctions, owners andoperators shall, to the extent practicable,maintain and operate any affected facilityincluding associated air pollution controlequipment in a manner consistent with goodair polution control practice for minimizingemissions. Determination of whetheracceptable operating and maintenanceprocedures are being used will be based oninformation available to the Administratorwhich may include, but is not limited to,monitoring results, opacity observations,review of operation and maintenanceprocedures, and inspection of the source.[40 CFR 60.11(d)]

None. None. None.

Page 60 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 No owner or operator subject to NSPS

standards in Part 60, shall build, erect,install, or use any article, machine,equipment or process, the use of whichconceals an emission which wouldotherwise constitute a violation of anapplicable standard. Such concealmentincludes, but is not limited to, the use ofgaseous diluents to achieve compliance withan opacity standard or with a standard whichis based on the concentration of a pollutantin the gases discharged to theatmosphere.[40 CFR 60.12]

None. None. None.

9 An owner or operator shall not cause to be

discharged into the atmosphere from anycoal processing and conveying equipment,coal storage system, or coal transfer andloading system processing coal, gases whichexhibit 20 percent opacity or greater.Opacity <= 20 %. [40 CFR 60.254(a)]

None. None. None.

Page 61 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U1 Ct 108170 - PC Boiler #1Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The requirements for this item are included

in GR1. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 62 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U1 Ct 108170 - PC Boiler #1Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The requirements for this item are included

in GR2. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS1 PC Boiler 1: Normal Firing using coal and/or No. 2 and/or No. 6 oil

Page 63 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U1 Ct 108170 - PC Boiler #1Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The requirements for this item are included

in GR3. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS2 PC Boiler #1: Start-up

Page 64 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U1 Ct 108170 - PC Boiler #1Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The requirements for this item are included

in GR4. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS3 PC Boiler #1: Shut-down

Page 65 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U2 Ct 108169 - PC Boiler #2Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The requirements for this item are included

in GR1. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 66 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U2 Ct 108169 - PC Boiler #2Operating Scenario:The requirements for this item are identical to those for: U1 OS1

OS1 PC Boiler 2: Normal firing using coal and/or No. 2 oil and/or No. 6 oil

Page 67 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U2 Ct 108169 - PC Boiler #2Operating Scenario:The requirements for this item are identical to those for: U1 OS2

OS2 PC Boiler 2: Start-up

Page 68 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U2 Ct 108169 - PC Boiler #2Operating Scenario:The requirements for this item are identical to those for: U1 OS3

OS3 PC Boiler 2: Shutdown

Page 69 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U3 Auxiliary BoilerOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The owner or operator of any utility boiler,

regardless of size, or any non-utility boilerwith a maximum gross heat input of50,000,000 Btu/hr shall not exceedconcentrations of CO <= 100 ppmdv @ 7%O2. [N.J.A.C. 7:27-16.8(b)2]

CO: Monitored by continuous emissionmonitoring system continuously, based onone calendar day (See ApplicableRequirement for GR1 PC Boilers #1 & 2,Summary Ref. #s 2 , 3, 4 and 5). [N.J.A.C.7:27-16.8(b)2]

CO: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously (See Applicable Requirementfor GR1 PC Boilers #1 & 2, Summary Ref.#s 2 , 3, 4 and 5). [N.J.A.C. 7:27-16.8(b)2]

None.

2 Annual emission rate based on maximum

hours of operation. VOC (Total) <= 0.26tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Annual emission limit based on maximum

hours of operation. NOx (Total) <= 5.69tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Annual emission limit based on maximum

hours of operation. CO <= 5.78 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Annual emission limit based on maximum

hours of operation. SO2 <= 10.64 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Annual emission limit based on maximum

hours of operation. TSP <= 0.67 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.67tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.67tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 70 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 For the auxiliary boiler, conduct a

comprehensive stack test at least 18 monthsprior to the expiration of the approvedoperating permit to demonstrate compliancewith the VOC, CO, NOx, TSP, and PM-10emission limits.Testing must be conducted at worst-casepermitted operating conditions with regardto meeting the applicable emissionstandards, but without creating an unsafecondition. Heat input (MMBtu/hr, HHV)shall be determined for each stack test.[N.J.A.C. 7:27-22.16(a)]

Monitored by stack emission testing prior topermit expiration date. Stack test shall beconducted for VOC, CO, NOx, TSP, andPM-10 emissions. [N.J.A.C. 7:27-22.16(o)]

Recordkeeping by stack test results prior topermit expiration date. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. Bureau of Code: 38008625 at lexpiration The protocprepared aElectronic another foERT progrhttp://wwwWithin 30 less than 6deadline, wmust contaschedule a A full stacBTS and a must be suEnforcemeperforming N.J.A.C. 7must be ceengineer ocopy of thmust be surenewal apprior to exRenewal.Test resultBtu (HHVparticulate and. [N.J.A

10 The owner or operator of any utility boiler,

regardless of size, or any non-utility boilerwith a maximum gross heat input of50,000,000 Btu/hr shall not exceedconcentrations of VOC (Total) <= 50 ppmdv@ 7% O2. [N.J.A.C. 7:27-16.8(b)1]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date (SeeApplicable Requirement for GR1 PC Boilers#1 & 2, Summary Ref. #s 2 , 3, 4 and 5).[N.J.A.C. 7:27-16.8(b)1]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date (SeeApplicable Requirement for GR1 PC Boilers#1 & 2, Summary Ref. #s 2 , 3, 4 and 5).[N.J.A.C. 7:27-16.8(b)1]

Stack Test and submischedule (GR1 PC B2 , 3, 4 an

Page 71 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

11 Hours of Operation <= 876 hr/yr based on a

consecutive 12-month period (rolling dailybasis). [N.J.A.C. 7:27-22.16(a)]

Hours of Operation: Monitored by hour/timemonitor each hour during operation, basedon a 1 hour block average. [N.J.A.C.7:27-22.16(o)]

Hours of Operation: Recordkeeping bymanual logging of parameter or storing datain a computer data system each hour duringoperation. [N.J.A.C. 7:27-22.16(o)]

None.

12 The permittee shall complete a tune-up

every 5 years as specified in 40 CFR63.7500(c). The tune-ups shall beconducted, as follows: (i) As applicable, inspect the burner, andclean or replace any components of theburner as necessary. The burner inspectionmay be delayed until the next scheduled unitoutage, not to exceed 36 months from theprevious inspection.(ii) Inspect the flame pattern, as applicable,and adjust the burner as necessary tooptimize the flame pattern. The adjustmentshould be consistent with the manufacturer'sspecifications, if available. (iii) Inspect the system controlling theair-to-fuel ratio, as applicable, and ensurethat it is correctly calibrated and functioningproperly. The inspection may be delayeduntil the next scheduled unit shutdown, notto exceed 36 months from the previousinspection.(iv) Optimize total emissions of carbonmonoxide. This optimization should beconsistent with the manufacturer'sspecifications, if available, and with anynitrogen oxide requirement to which the unitis subject. [40 CFR 63.7540(a)(10)]

Monitored by periodic emission monitoringonce initially and once every 5 years. Measure the concentrations in the effluentstream of carbon monoxide (CO) in partsper million, by volume, and oxygen involume percent, before and after theadjustments are made (measurements maybe either on a dry or wet basis, as long as itis the same basis before and after theadjustments are made). Measurements maybe taken using a portable CO analyzer. [40CFR 63.7540(a)(10)(v)]

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem once initially and once every 5 years.The permittee shall keep the followingrecords for a period of 5 years following thedate of each recorded action to documentconformance with once every 5 yearstune-up:Records identifying each boiler, the date oftune-up, the procedures followed fortune-ups and the manufacturer'sspecifications to which the boiler was tuned.Maintain on-site and submit if requested bythe Administrator, a report containing thefollowing information: (A) Theconcentrations of CO in the effluent streamin parts per million by volume, and oxygenin volume percent, measured at high fire ortypical operating load, before and after thetune-up of the boiler or process heater; (B)A description of any corrective actions takenas a part of the tune-up; and (C) The typeand amount of fuel used over the 12 monthsprior to the tune-up, but only if the unit wasphysically and legally capable of using morethan one type of fuel during that period.Units sharing a fuel meter may estimate thefuel used by each unit. [40 CFR63.7540(a)(10)(vi)]

None.

Page 72 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U3 Auxiliary BoilerOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions, exclusive of visible

condensed water vapor, except for a periodof not longer than three minutes in anyconsecutive 30-minute period. [N.J.A.C.7:27-3.2(c)] & [N.J.A.C. 7:27-22.16(e)]

Monitored by continuous opacity monitorcontinuously, based on any consecutive30-minute period. [N.J.A.C. 7:27- 3.2(c)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27- 3.2(c)]

None.

2 Particulate emission limit from the

combustion of fuel based on rated heat inputof source. Particulate Emissions <= 13.7lb/hr. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

3 Maximum emission rate from

preconstruction permit. TSP <= 1.54 lb/hr.[N.J.A.C. 7:27-22.16(e)]

TSP: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. [N.J.A.C. 7:27-22.16(o)]

TSP: Recordkeeping by stack test resultsprior to permit expiration date. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. 

4 Sulfur Content in Fuel <= 500 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective through June30, 2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

5 Sulfur Content in Fuel <= 15 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective from July 1,2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

6 The owner or operator of a non-utility boiler

shall not exceed the maximum allowableNOx emission rate based on fuel/boiler typeand firing method. NOx (Total) <= 0.08lb/MMBTU. [N.J.A.C. 7:27-19.7(i)2]

NOx (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults prior to permit expiration date.[N.J.A.C. 7:27-22.16(o)]

None.

7 Maximum emission rate based on

preconstruction permit. TSP <= 0.02lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

TSP: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. [N.J.A.C. 7:27-22.16(o)]

TSP: Recordkeeping by stack test resultsprior to permit expiration date. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. 

8 Maximum gross heat input based on

preconstruction permit. Maximum GrossHeat Input <= 77 MMBTU/hr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

OS1 Auxiliary Boiler Normal Operation

Page 73 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 Boiler fuel type limited to distillate fuel oil

based on preconstruction permit. [N.J.A.C.7:27-22.16(e)]

None. Recordkeeping by invoices / bills of lading /

certificate of analysis per delivery showingmaterials delivered. [N.J.A.C.7:27-22.16(o)]

None.

10 Annual distillate fuel oil limit based on 876

hours of operation is 481,800 gallons/anyconsecutive 12 months.Gallons of distillate fuel oil consumedduring any consecutive 12-month periodshall be calculated by adding the oilconsumption for a given month to thegallons of oil consumed during thepreceding 11-month period.This procedure will begin the first fullmonth following the final issuance of theOperating Permit. This accounting will notinclude oil consumption for the monthsprior to the Operating Permit approval.Distillate Fuel Oil Usage <= 481.8 Mgals.[N.J.A.C. 7:27-22.16(a)]

Fuel Oil Usage: Monitored by fuelflow/firing rate instrument continuously,based on a consecutive 12 month period(rolling 1 month basis). [N.J.A.C.7:27-22.16(o)]

Fuel Oil Usage: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously or manual logging ofparameter, daily (permanently bound).Compliance shall be based on a twelveconsecutive month period computed withmonthly sums. [N.J.A.C. 7:27-22.16(o)]

None.

11 The low NOx burners and flue gas

recirculation system (FGR) shall beoperational at all times the auxiliary boiler isoperating. Flue Gas Recirculation Rate >=12 % of flue gas. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

12 The auxiliary boiler shall not be operated at

the same time as either PC boiler, exceptwhen steam is required during PC boilerstart-up, shutdown, testing, or emergencysituations. [N.J.A.C. 7:27-22.16(e)]

Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27-22.16(o)]

None.

13 Maximum emission rate from

preconstruction permit. NOx (Total) <= 13lb/hr. [N.J.A.C. 7:27-22.16(e)]

NOx (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. [N.J.A.C.7:27-22.16(o)]

NOx (Total): Recordkeeping by stack testresults prior to permit expiration date.[N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. 

14 Maximum concentration value from

preconstruction permit. CO <= 100 ppmdv@ 7% O2. [N.J.A.C. 7:27-22.16(e)]

CO: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. [N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit expiration date. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. 

Page 74 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

15 Maximum emission rate from

preconstruction permit. PM-10 (Total) <=1.54 lb/hr. [N.J.A.C. 7:27-22.16(e)]

PM-10 (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. [N.J.A.C.7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults prior to permit expiration date.[N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. 

16 Maximum emission rate, PM-2.5 (Total) <=

1.54 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

17 Maximum emission rate based on

preconstruction permit. PM-10 (Total) <=0.02 lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

PM-10 (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. [N.J.A.C.7:27-22.16(o)]

PM-10 (Total): Recordkeeping by stack testresults prior to permit expiration date.[N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. 

18 Maximum emission rate. PM-2.5 (Total) <=

0.02 lb/MMBTU. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

19 Maximum emission rate from

preconstruction permit. VOC (Total) <= 0.6lb/hr. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. [N.J.A.C.7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date.[N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. 

20 Maximum emission rate from

preconstruction permit. VOC (Total) <=0.008 lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. [N.J.A.C.7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date.[N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. 

21 Maximum concentration value from

preconstruction permit. VOC (Total) <= 16ppmdv @ 7% O2. [N.J.A.C. 7:27-22.16(e)]

VOC (Total): Monitored by stack emissiontesting prior to permit expiration date, basedon the average of three Departmentvalidated stack test runs. [N.J.A.C.7:27-22.16(o)]

VOC (Total): Recordkeeping by stack testresults prior to permit expiration date.[N.J.A.C. 7:27-22.16(o)]

Stack Test and submischedule. 

22 Maximum emission rate based on

preconstruction permit. CO <= 13.2 lb/hr.[N.J.A.C. 7:27-22.16(e)]

CO: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. [N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit expiration date. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. 

23 Maximum emission rate based on

preconstruction permit. CO <= 0.172lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

CO: Monitored by stack emission testingprior to permit expiration date, based on theaverage of three Department validated stacktest runs. [N.J.A.C. 7:27-22.16(o)]

CO: Recordkeeping by stack test resultsprior to permit expiration date. [N.J.A.C.7:27-22.16(o)]

Stack Test and submischedule. 

Page 75 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

24 The owner or operator of an

industrial/commercial/institutional boiler orother indirect heat exchanger with a grossheat input of at least five million BTU perhour or more shall adjust the combustionprocess annually in the same quarter of eachcalendar year. The adjustment of thecombustion process shall be done inaccordance with the procedure set forth atN.J.A.C. 7:27-19.16. [N.J.A.C.7:27-16.8(c)] and [N.J.A.C. 7:27-19.7(g)]

Monitored by periodic emission monitoringannually. The owner or operator shallperform the adjustment of the combustionprocess in accordance with the specificprocedures for combustion adjustmentmonitoring specified in NJDEP TechnicalManual 1005 and the procedure set forth atN.J.A.C. 7:27-19.16(a) as follows: 1.Inspectthe burner, and clean or replace anycomponents of the burner as necessary; 2.Inspect the flame pattern and make anyadjustments to the burner necessary tooptimize the flame pattern consistent withthe manufacturer's specifications; 3. Inspectthe system controlling the air-to-fuel ratio,and ensure that it is correctly calibrated andfunctioning properly; 4. Minimize the totalemissions of NOx and CO consistent withthe manufacturer's specifications; 5.Measure the concentrations in the effluentstream of NOx, CO and O2 in ppmvd,before and after the adjustment is made; and6. Convert the emission values of NOx, COand O2 concentrations measured inlb/MMBTU according to the followingformula: Lb/MMBTU = ppmvd * MW * Fdry factor * O2 correctionfactor/387,000,000, where: ppmvd is theconcentration in parts per million byvolume, dry basis, of NOx or CO; MW isthe Molecular Weight for NOx=46lb/lb-mole, CO=28 lb/lb-mole; F Dry factorfor: Natural Gas = 8,710 dscf/MMBTU,Residual or fuel oil = 9,190 dscf/MMBTU;O2 correction factor: (20.9%)/(20.9% - O2measured), where O2 measured is percentoxygen on a dry basis. [N.J.A.C.7:27-19.16(a)]

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon performing combustionadjustment of the following information foreach adjustment: 1. The date of theadjustment and the times at which it beganand ended; 2. The name, title and affiliationof the person who made the adjustment; 3.The NOx and CO concentrations in theeffluent stream, in ppmvd, before and aftereach actual adjustment was made; 4. Theconcentration of O2 (in percent dry basis) atwhich the CO and NOx concentrations weremeasured; 5. A description of any correctiveaction taken; 6. Results from any subsequenttest performed after taking any correctiveaction, including concentrations andconverted emission values in (lb/MMBTU);7. The type and amount of fuel used over the12 months prior to the annual adjustment; 8.Any other information which theDepartment or the EPA has required as acondition of approval of any permit orcertificate issued for the source operation.The records must be retained for a minimumof five years and to be made readilyaccessible to the Department upon request.[N.J.A.C. 7:27-19.16(b)]

Submit a roperator shcombustiowithin 45 combustioshall be suwww.njdesubmitting http://www[N.J.A.C. 7:27-19.16

Page 76 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

25 The owner or operator of the adjusted

equipment or source operation shall ensurethat the operating parameter settings areestablished and recorded after thecombustion process is adjusted and that theadjusted equipment or source operation ismaintained to operate consistent with theannual adjustment. [N.J.A.C. 7:27-19.16(e)]

Other: Monitored by the operatingparameter settings that are established afterthe combustion process is adjusted in orderto operate consistent with the annualadjustment. [N.J.A.C. 7:27-19.16(e)].

Other: The owner or operator shall recordthe operating parameter settings that areestablished after the combustion process isadjusted and retain until the next annualadjustment, to be made readily accessible tothe Department upon request. [N.J.A.C.7:27-19.16(e)].

None.

26 Maximum emission rate from

preconstruction permit. SO2 <= 24.3 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

27 Maximum emission rate based on

preconstruction permit. SO2 <= 0.315lb/MMBTU. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

28 Sulfur content in distillate fuel oil

combusted in the boiler shall not exceed0.5% sulfur by weight. This fuel oil sulfurlimit applies at all times, including periodsof startup, shutdown and malfunction.Sulfur Content in Fuel <= 0.5% sulfur byweight. [40 CFR 60.42c(d)] &. [40 CFR60.42c(i)]

Other: Sulfur Content in Fuel Oil. PerDelivery.[40 CFR 60.42c(d)].

Other: Keep certificate of analysis from fuelsupplier showing fuel sulfur content. PerDelivery.[40 CFR 60.42c(d)].

Other (proapproved 30th day fhalf in acc[40 CFR 6

29 Opacity <= 20 % except for one 6-minute

period per hour of not more than 27%opacity. This opacity standard does notapply during periods of startup, shutdown ormalfunction. [40 CFR 60.43c(c)]

Opacity: Monitored by continuous opacitymonitor continuously, based on 6 minuteblocks. [40 CFR 60.43c(c)]

Opacity: Recordkeeping by data acquisitionsystem (DAS) / electronic data storagecontinuously. [40 CFR 60.43c(c)]

None.

30 The owner or operator shall maintain

records, and report to the Administrator, allinformation specified at 40 CFR 60.48c(e).[40 CFR 60.48c(d)]

Other: See relevant applicable requirementsin U3, Auxiliary Boiler, OS1 AuxiliaryBoiler - Normal Operation.[40 CFR60.48c(d)].

Other: See relevant applicable requirementsin U3, Auxiliary Boiler, OS1 AuxiliaryBoiler - Normal Operation.[40 CFR60.48c(e)].

Submit a rschedule. following The reportRegion II Regional Osemiannuathe 30th dreporting prequiremeAuxiliary CFR 60.48

Page 77 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

31 The owner or operator shall record the

amount of each fuel combusted in the uniteach operating day.[40 CFR 60.48c(g)]

Monitored by fuel flow/firing rateinstrument continuously, based on noaveraging period. [40 CFR 60.48c(g)]

Recordkeeping by manual logging ofparameter daily. [40 CFR 60.48c(g)]

None.

32 Semiannual Reports for Sulfur Content:

The semiannual report shall include thefollowing information:1) Calendar dates covered in the reportingperiod.2) Each 30-day average sulfur content(weight percent) calculated during thereporting period, ending with the last 30-dayperiod; reasons for any noncompliance withthe emission standards; and a description ofcorrective actions taken.3) Each 30-day average percent ofpotential SO2 emission rate calculatedduring the reporting period, ending with thelast 30-day period; reasons for anynoncompliance with the emission standards;and a description of corrective actions taken.4) Identification of any steam generatingunit operating days for which SO2 or diluent(oxygen or carbon dioxide) data have notbeen obtained by an approved method for atleast 75 percent of the operating hours;justification for not obtaining sufficientdata; and a description of corrective actionstaken.5) Identification of any times whenemissions data have been excluded from thecalculation of average emission rates;justification for excluding data; and adescription of corrective actions taken ifdata have been excluded for periods otherthan those during which coal or oil were notcombusted in the steam generating unit. [40CFR 60.48c(e)]

Other: See applicable requirement.[40 CFR60.48c(e)].

Other: See applicable requirement.[40 CFR60.48c(e)].

Other (proapplicable 

Page 78 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

33 Semiannual Reports for Sulfur Content:

The semiannual report shall include thefollowing information:6) Identification of the F factor used incalculations, method of determination, andtype of fuel combusted.7) Identification of whether averages havebeen otained based on CEMS rahter thanmanual sampling methods.8) If a CEMS is used, identification of anytimes when the pollutant concentrationexceeded the full span of the CEMS.9) If a CEMS is used, description of anymodifications to the CEMS that could affectthe ability of the CEMS to comply withPerformance Specifications 2 or 3 (apendixB)10) If a CEMS is used, results of dailyCEMS drift tests and quarterly accuracyassessments as required under appendix F,Procedure 1.11) If fuel supplier certification is used todemonstrate compliance, records of fuelsupplier certification and a certifiedstatement signed by the owner or operator ofthe affected facility that the records of fuelsupplier certifications sumitted represent allof the fuel combusted during the reportingperiod, the name of the oil supplier, and sstatement from the oil supplier that the oilcomplies with the specifications under thedefinition of distillate oil in Sec. 60.41c. [40CFR 60.48c(e)]

Other: See applicable requirement.[40 CFR60.48c(e)].

Other: See applicable requirement.[40 CFR60.48c(e)].

Other (proapplicable 

Page 79 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U3 Auxiliary BoilerOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions, exclusive of visible

condensed water vapor, except for a periodof not longer than three minutes in anyconsecutive 30-minute period. [N.J.A.C.7:27-3.2(a)] & [N.J.A.C. 7:27- 3.2(c)]

Monitored by continuous opacity monitorcontinuously, based on any consecutive30-minute period. [N.J.A.C. 7:27- 3.2(c)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27- 3.2(c)]

None.

2 Particulate emission limit from the

combustion of fuel based on rated heat inputof source. Particulate Emissions <= 13.7lb/hr. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

3 Sulfur Content in Fuel <= 500 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective through June30, 2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

4 Sulfur Content in Fuel <= 15 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective from July 1,2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

5 Do not exceed 50 ppmdv VOC at 7%

Oxygen. VOC (Total) <= 50 ppmdv @ 7%O2. [N.J.A.C. 7:27-16.8(b)1]

None. None. None.

6 Do not exceed 100 ppmdv CO at 7%

Oxygen. CO <= 100 ppmdv @ 7% O2.[N.J.A.C. 7:27-16.8(b)2]

None. None. None.

7 The owner or operator of a non-utility boiler

shall not exceed the maximum allowableNOx emission rate based on fuel/boiler typeand firing method. NOx (Total) <= 0.08lb/MMBTU. [N.J.A.C. 7:27-19.7(i)2]

None. None. None.

8 Maximum gross heat input based on

preconstruction permit. Maximum GrossHeat Input <= 77 MMBTU/hr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

OS2 Auxiliary Boiler: Start-up

Page 80 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 The low NOx burners and flue gas

recirculation system (FGR) shall beoperational at all times the auxiliary boiler isoperating. Flue Gas Recirculation Rate >=12 % of flue gas. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

10 Start-up is defined as that period of time

from boiler ignition until steam is availablefor customer use. Start-up Period <= 3hours. [N.J.A.C. 7:27-22.16(e)]

Start-up Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Start-up Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]

None.

11 Sulfur content in distillate fuel oil

combusted in the boiler shall not exceed0.5% sulfur by weight. This fuel oil sulfurlimit applies at all times, including periodsof startup, shutdown and malfunction.Sulfur Content in Fuel <= 0.5% sulfur byweight. [40 CFR 60.42c(d)] &. [40 CFR60.42c(i)]

Other: Sulfur Content in Fuel Oil. PerDelivery.[40 CFR 60.42c(d)].

Other: Keep certificate of analysis from fuelsupplier showing fuel sulfur content. PerDelivery.[40 CFR 60.42c(d)].

Other (proapproved 30th day fhalf in acc[40 CFR 6

Page 81 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U3 Auxiliary BoilerOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions, exclusive of visible

condensed water vapor, except for a periodof not longer than three minutes in anyconsecutive 30-minute period. [N.J.A.C.7:27-3.2(a)] & [N.J.A.C. 7:27- 3.2(c)]

Monitored by continuous opacity monitorcontinuously, based on any consecutive30-minute period. [N.J.A.C. 7:27- 3.2(c)]

Recordkeeping by data acquisition system(DAS) / electronic data storagecontinuously. [N.J.A.C. 7:27- 3.2(c)]

None.

2 Particulate emission limit from the

combustion of fuel based on rated heat inputof source. Particulate Emissions <= 13.7lb/hr. [N.J.A.C. 7:27- 4.2(a)]

None. None. None.

3 Sulfur Content in Fuel <= 500 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective through June30, 2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

4 Sulfur Content in Fuel <= 15 ppmw.

Maximum allowable sulfur content indistillate oil by fuel oil type/viscosity andgeographical zone. (Effective from July 1,2016). [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery. [N.J.A.C.7:27-22.16(o)]

None.

5 Do not exceed 50 ppmdv VOC at 7%

Oxygen. VOC (Total) <= 50 ppmdv @ 7%O2. [N.J.A.C. 7:27-16.8(b)1]

None. None. None.

6 Do not exceed 100 ppmdv CO at 7%

Oxygen. CO <= 100 ppmdv @ 7% O2.[N.J.A.C. 7:27-16.8(b)2]

None. None. None.

7 The owner or operator of a non-utility boiler

shall not exceed the maximum allowableNOx emission rate based on fuel/boiler typeand firing method. NOx (Total) <= 0.08lb/MMBTU. [N.J.A.C. 7:27-19.7(i)2]

None. None. None.

8 Maximum gross heat input based on

preconstruction permit. Maximum GrossHeat Input <= 77 MMBTU/hr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

OS3 Auxiliary Boiler: Shutdown

Page 82 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 The low NOx burners and flue gas

recirculation system (FGR) shall beoperational at all times the auxiliary boiler isoperating. Flue Gas Recirculation Rate >=12 % of flue gas. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

11 Shutdown is defined as that period of time

after which steam is no longer available forcustomer use until cessation of fuel flow tothe auxiliary boiler. Shutdown Period <= 15minutes. [N.J.A.C. 7:27-22.16(e)]

Shutdown Period: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Shutdown Period: Recordkeeping by dataacquisition system (DAS) / electronic datastorage continuously. [N.J.A.C.7:27-22.16(o)]

None.

10 Sulfur content in distillate fuel oil

combusted in the boiler shall not exceed0.5% sulfur by weight. This fuel oil sulfurlimit applies at all times, including periodsof startup, shutdown and malfunction.Sulfur Content in Fuel <= 0.5% sulfur byweight. [40 CFR 60.42c(d)] &. [40 CFR60.42c(i)]

Other: Sulfur Content in Fuel Oil. PerDelivery.[40 CFR 60.42c(d)].

Other: Keep certificate of analysis from fuelsupplier showing fuel sulfur content. PerDelivery.[40 CFR 60.42c(d)].

Other (proapproved 30th day fhalf in acc[40 CFR 6

Page 83 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U10 Ct 115560 - Coal UnloaderOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

4 Based on preconstruction permit, Hours of

Operation <= 1,030 hr/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

5 Annual limit of bituminous coal unloaded

from rail cars to hopper, received by apronfeeder and transferred to stack-out conveyor.Total Material Transferred <= 900,000tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Annual emission limit based on maximum

hours of operation. TSP <= 0.175 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.175tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.175tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 84 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U10 Ct 115560 - Coal UnloaderOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-22.16(a)]

Monitored by visual determination eachmonth during operation, based on theaveraging period as per Departmentapproved test method. Visual inspectionsshall consist of a visual survey to identify ifthe stack has visible emissions (other thancondensed water vapor) greater than theprescribed standard. If visible emissions areobserved, the permittee shall:(1) Verify that the equipment and/or controldevice causing the emissions is operatingaccording to manfacturer's specificationsand the operating permit compliance plan.If the equipment and/or control device arenot operating properly, the permittee shalltake corrective action immediately toeliminate the excess emissions. Thepermittee must report any permit violation tothe NJDEP pursuant to N.J.A.C. 7:27-22.19.(2) If the corrective action taken in step (1)does not correct the visible emissionsproblem within 24 hours, the applicant shallperform a check via a certified reader inaccordance with N.J.A.C. 7:27B-2. Such atest shall be conducted each shift whenoperating until corrective action is taken tosuccessfully correct the visible emissionsproblem. The permittee must report anycontinuing permit violation pursuant toN.J.A.C.7:27-22.19. [N.J.A.C.7:27-22.16(o)]

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem each month during operation(permanently bound). The permittee mustretain the following records: (1) date andtime of inspection, (2) emission pointnumber, (3) operational status of equipment,(4) observed results and conclusions, (5)description of corrective action if needed,(6) date and time visible emission problemwas solved, if applicable, (7)N.J.A.C.7:27B-2 results if conducted, and(8) name of person(s) conducting inspection.[N.J.A.C. 7:27-22.16(o)]

None.

2 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS1 Coal Unloader

Page 85 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

3 Fugitive dust emissions shall be controlled

by wet suppression and/or surfactant asnecessary. The surfactant spray to be usedfor wet suppression of coal dust must bewater or nonpetroleum base surfactant.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from

preconstruction permit. TSP <= 0.34 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.34lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.34lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 86 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U11 Ct 115560 - Apron Feeder & Stack-out Conveyor TailOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period. [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

4 Based on preconstruction permit, Hours of

Operation <= 1,030 hr/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

5 Annual limit of bituminous coal unloaded

from rail cars to hopper, received by apronfeeder and transferred to stack-out conveyor.Total Material Transferred <= 900,000tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Annual emission limit based on maximum

hours of operation. TSP <= 0.001 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

7 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.001tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.001tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 87 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U11 Ct 115560 - Apron Feeder & Stack-out Conveyor TailOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Maximum emission rate from

preconstruction permit. TSP <= 0.001 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.001lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.001lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 CD11: Pressure Drop Range across the

Baghouse while equipment is operating,limited to between 1.5 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS1 Coal Unloading Apron Feeder

Page 88 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U11 Ct 115560 - Apron Feeder & Stack-out Conveyor TailOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Maximum emission rate from

preconstruction permit. TSP <= 0.001 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.001lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.001lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 1.5 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS2 Stack-out Conveyor Tail

Page 89 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U13 Ct 115562 - Reclaim Conveyor TailOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Annual emission limit based on maximum

hours of operation. TSP <= 0.00063 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <=0.00063 tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <=0.00063 tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 90 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U13 Ct 115562 - Reclaim Conveyor TailOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Fugitive dust emissions from coal conveyor

transfer points shall be controlled by fabricfilters (bag-type dust collectors). [N.J.A.C.7:27-22.16(e)]

None. None. None.

5 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

6 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

7 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

OS1 Reclaim Conveyor Tail

Page 91 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Based on preconstruction permit, Hours of

Operation <= 1,800 hr/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

9 Annual limit of bituminous coal transferred

from active coal pile to reclaim conveyor.Total Material Transferred <= 900,000tons/yr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

10 Maximum emission rate from

preconstruction permit. TSP <= 0.0007lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

11 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0007 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

12 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0007 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 92 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U14 Ct 099327 - 6700 Crusher Bldg. Baghouse.Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

5 Based on preconstruction permit, Hours of

Operation <= 1,800 hr/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

6 Annual limit of bituminous coal transferred

from reclaim conveyor for crushing/sizing totransfer conveyor. Total MaterialTransferred <= 900,000 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

7 Annual emission limit based on maximum

hours of operation. TSP <= 0.163 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

8 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.163tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 93 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

9 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.163tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 94 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U14 Ct 099327 - 6700 Crusher Bldg. Baghouse.Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions from coal conveyor

transfer points shall be controlled by fabricfilters (bag-type dust collectors). [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 CD14: Pressure Drop Range across the

Baghouse while equipment is operating,limited to between 1.5 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS1 Reclaim Conveyor Head

Page 95 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U14 Ct 099327 - 6700 Crusher Bldg. Baghouse.Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 The coal crusher shall be enclosed and

provided with a bag-type dust collector toprevent fugitive dust emissions. [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 Maximum emission rate from

preconstruction permit. TSP <= 0.09 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.09lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.09lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 1.5 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS2 Crusher No. 1

Page 96 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U14 Ct 099327 - 6700 Crusher Bldg. Baghouse.Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 The coal crusher shall be enclosed and

provided with a bag-type dust collector toprevent fugitive dust emissions. [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 Maximum emission rate from

preconstruction permit. TSP <= 0.09 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.09lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.09lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 1.5 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS3 Crusher No.2

Page 97 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U14 Ct 099327 - 6700 Crusher Bldg. Baghouse.Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions from coal conveyor

transfer points shall be controlled by fabricfilters (bag-type dust collectors). [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 Maximum emission rate from

preconstruction permit. TSP <= 0.0006lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0006 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0006 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 1.5 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS4 Transfer Conveyor Tail

Page 98 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period. [N.J.A.C.7:27-6.2(d)] & [N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

4 Based on preconstruction permit, Hours of

Operation <= 1,800 hr/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

5 Annual limit of bituminous coal transferred

from reversible conveyor to (2) silo feedconveyors to (8) coal silos. Total MaterialTransferred <= 900,000 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

6 Annual emission limit based on maximum

hours of operation. TSP <= 0.0033 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

7 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <=0.0033 tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <=0.0033 tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 99 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

2 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Fugitive dust emissions from coal conveyor

transfer points shall be controlled by fabricfilters (bag-type dust collectors). [N.J.A.C.7:27-22.16(e)]

None. None. None.

4 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0003 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0003 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

6 Maximum emission rate from

preconstruction permit. TSP <= 0.0003lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

7 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

OS1 Transfer Conveyor Head

Page 100 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions from coal conveyor

transfer points shall be controlled by fabricfilters (bag-type dust collectors). [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0009lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0009 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0009 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS2 Silo Feed System - Conveyor & Tripper #1

Page 101 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions from coal conveyor

transfer points shall be controlled by fabricfilters (bag-type dust collectors). [N.J.A.C.7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0009lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0009 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0009 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS3 Silo Feed System - Conveyor & Tripper #2

Page 102 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS4 Coal Silo (1)

Page 103 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS5 Coal Silo (2)

Page 104 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS6 Coal Silo (3)

Page 105 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS7 Coal Silo (4)

Page 106 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS8 Coal Silo (5)

Page 107 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS9 Coal Silo (6)

Page 108 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem daily. [N.J.A.C. 7:27-22.16(o)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS10 Coal Silo (7)

Page 109 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U18 Ct 115563 - Coal Silo BayOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

3 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse, while equipment is operating,limited to between 3 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by manual logging ofparameter daily. [N.J.A.C. 7:27-22.16(a)]

None.

4 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

5 Maximum emission rate from

preconstruction permit. TSP <= 0.0002lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from operating

permit application. PM-10 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. PM-2.5 (Total) <=0.0002 lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS11 Coal Silo (8)

Page 110 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U30 Ct 115564 - Ash Transfer SystemOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Annual emission limit based on maximum

hours of operation. TSP <= 0.048 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

2 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.048tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.048tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 111 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U30 Ct 115564 - Ash Transfer SystemOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

6 Maximum emission rate from

preconstruction permit. TSP <= 0.027 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

7 The Ash Transfer System consists of four

filter separators. Each filter separator shallbe equipped with a differential pressuregauge and a dust detector. The differentialpressure gauges shall give a high differentialpressure alarm and a high high differentialpressure system shutdown. A shutdown ofthe system shall be triggered when leakageof dust is detected by the dust detectors.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS1 Ash Transfer System

Page 112 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.027lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

9 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.027lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

10 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

11 Based on preconstruction permit, Hours of

Operation <= 3,560 hr/yr. [N.J.A.C.7:27-22.16(a)]

None. None. None.

12 Annual limit of ash transferred from PC

boiler's baghouse to ash storage silo. TotalMaterial Transferred <= 160,200 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 113 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U34 Ct 115558 - Ash Recycle SiloOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Annual emission limit based on maximum

hours of operation. TSP <= 0.004 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.004tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.004tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 114 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U34 Ct 115558 - Ash Recycle SiloOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

6 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse (CD34), while equipment isoperating, limited to between 3 and 9 inchesH2O column. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by data acquisition system(DAS) / electronic data storage daily.[N.J.A.C. 7:27-22.16(o)]

None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS1 Ash Recycle Silo

Page 115 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Annual limit of ash transferred to ash

recycle silo. Total Material Transferred <=35,040 tons/yr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

9 Maximum emission rate from

preconstruction permit. TSP <= 0.001 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

10 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.001lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

11 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.001lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 116 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U35 Ash Mixer normal operation (mix ash with water)Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Annual emission limit based on maximum

hours of operation. TSP <= 0.2 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.2tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.2tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 117 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U35 Ash Mixer normal operation (mix ash with water)Operating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Dust emissions from the ash mixer shall be

controlled by fabric filters (cartridge-typedust collectors) at all times during operation.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 The permittee shall conduct cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

6 Annual limit of ash transferred from silo to

rail cars or trucks (excluding water). TotalMaterial Transferred <= 160,200 tons/yr.[N.J.A.C. 7:27-22.16(a)]

None. None. None.

7 Maximum emission rate from operating

permit application. TSP <= 0.09 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

OS1 Ash Mixer normal operation (mix ash with water)

Page 118 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.09lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

9 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.09lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

10 Based on operating permit application,

Hours of Operation <= 4,380 hr/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 119 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U36 Ct 115559 - Ash Storage Silo and UnloaderOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Annual emission limit based on maximum

hours of operation. TSP <= 0.048 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.048tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.048tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 120 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U36 Ct 115559 - Ash Storage Silo and UnloaderOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 CD36: Pressure Drop Range across the

Baghouse, while equipment is operating,limited to between 0.5 and 9 inches H2Ocolumn. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by data acquisition system(DAS) / electronic data storage daily.[N.J.A.C. 7:27-22.16(o)]

None.

6 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

7 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

OS1 Ash Storage Silo and Unloader

Page 121 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Based on preconstruction permit, Hours of

Operation <= 1,600 hr/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

9 Annual limit of ash transferred from silo to

enclosed rail cars. Total MaterialTransferred <= 160,200 tons/yr. [N.J.A.C.7:27-22.16(e)]

None. None. None.

10 Maximum emission rate from

preconstruction permit. TSP <= 0.06 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

11 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.06lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

12 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.06lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

Page 122 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U37 Ct 099322 - Lime SiloOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Annual emission limit based on maximum

hours of operation. TSP <= 0.107 tons/yr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

2 Annual emission limit based on maximum

hours of operation. PM-10 (Total) <= 0.107tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

3 Annual emission limit based on maximum

hours of operation. PM-2.5 (Total) <= 0.107tons/yr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

OS Summary

Page 123 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U37 Ct 099322 - Lime SiloOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Maximum allowable emission rate for

particulates <= 0.5 lb/hr. [N.J.A.C. 7:27-6.2(a)]

None. None. None.

2 Opacity may be no greater than 20%

exclusive of visible condensed water, exceptfor a period of not longer than 3 minutes inany consecutive 30-minute period.For compliance with the monitoring andrecordkeeping requirements for the visibleemission standards, the permittee shallconduct required visual inspections duringdaylight hours. [N.J.A.C. 7:27-6.2(d)] &[N.J.A.C. 7:27- 6.2(e)]

None. None. None.

3 No visible emissions to the outdoor air from

the coal, ash and lime handling operations,except for a period of not longer than 3minutes in any consecutive 30-minuteperiod. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

4 Fugitive dust emissions shall be controlled

by fabric filters (bag-type dust collectors).[N.J.A.C. 7:27-22.16(e)]

None. None. None.

5 Based on operating permit application,

Operating Pressure Drop Range across thebaghouse (CD17), while equipment isoperating, limited to between 3 and 9 inchesH2O column. [N.J.A.C. 7:27-22.16(a)]

Other: Monitored by magnehelic differentialpressure gauge, daily. The permittee shallinstall, calibrate and maintain the monitor(s)in accordance with the manufacturer'sspecifications.[N.J.A.C. 7:27-22.16(o)].

Recordkeeping by data acquisition system(DAS) / electronic data storage daily.[N.J.A.C. 7:27-22.16(o)]

None.

6 The permittee shall conduct bag cleaning,

maintenance and replacement on a schedulenecessary to achieve the required particulateremoval efficiency as specified by themanufacturer. [N.J.A.C. 7:27-22.16(a)]

None. Recordkeeping by manual logging of

parameter or storing data in a computer datasystem upon occurrence of event. Thepermittee shall record each instance of bagcleaning and bag replacement. [N.J.A.C.7:27-22.16(o)]

None.

7 All outdoor conveyor belts shall be covered

with extended hoods. [N.J.A.C.7:27-22.16(e)]

None. None. None.

OS1 Lime Silo

Page 124 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Based on operating permit application,

Maximum Operating Exhaust Gas FlowRate <= 2500 acfm [N.J.A.C. 7:27-22.16(a)]

None. None. None.

9 Hours of Operation <= 2,000 hr/yr.

[N.J.A.C. 7:27-22.16(a)]

Hours of Operation: Monitored by hour/timemonitor continuously. The permittee shallcalculate hours of operations of eachdelivery of lime by dividing the amount oflime delivered (tons per delivery) bymaterial handling rate (40 tons per hour).[N.J.A.C. 7:27-22.16(o)]

Hours of Operation: Recordkeeping bymanual logging of parameter or storing datain a computer data system per delivery.[N.J.A.C. 7:27-22.16(o)]

None.

10 Annual limit of pebble lime throughput.

Total Material Transferred <= 80,000tons/yr. [N.J.A.C. 7:27-22.16(e)]

Total Material Transferred: Monitored bymaterial feed/flow monitoring continuously.The permittee shall record the amount ofpebble lime loaded into the silo for eachdelivery. [N.J.A.C. 7:27-22.16(o)]

Total Material Transferred: Recordkeepingby manual logging of parameter or storingdata in a computer data system per delivery.[N.J.A.C. 7:27-22.16(o)]

None.

11 TSP <= 0.107 lb/hr. [N.J.A.C.

7:27-22.16(a)]

None. None. None.

12 PM-10 (Total) <= 0.107 lb/hr. [N.J.A.C.

7:27-22.16(a)]

None. None. None.

13 PM-2.5 (Total) <= 0.107 lb/hr. [N.J.A.C.

7:27-22.16(a)]

None. None. None.

Page 125 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U38 Ct 117297 - Diesel Fire PumpOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Each emergency generator shall be located

at the facility and produce mechanical orthermal energy, or electrical powerexclusively for use at the facility. Eachemergency generator shall be operated only:1. During the performance of normal testingand maintenance procedures, includingother fire protection equipment, asrecommended in writing by the fire pump orfire protection system manufacturer and/oras required in writing by a Federal or Statelaw or regulation,2. When there is power outage or theprimary source of mechanical or thermalenergy fails because of an emergency, or3. When there is a voltage reduction issuedby PJM and posted on the PJM internetwebsite (www.pjm.com) under the"emergency procedures" menu. [N.J.A.C.7:27-22.16(a)] and [N.J.A.C. 7:27-19.1]

Monitored by hour/time monitorcontinuously. [N.J.A.C. 7:27-22.16(o)]

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem at the approved frequency. Theowner or operator shall maintain on site andrecord in a logbook or computer datasystem, the following information:1. Once per month, the total operating timefrom the generator's hour meter.2. For each time the emergency generator isspecifically operated for testing ormaintenance: i. The reason for its operation; ii. The date(s) of operation and the startup and shut down time; iii. The total operating time for testing ormaintenance based on the generator's hourmeter; and iv. The name of the operator; and3. If a voltage reduction is the reason for theuse of the emergency generator, a copy ofthe voltage reduction notification from PJMor other documentation of the voltagereduction.The owner or operator of an emergencygenerator shall maintain the above recordsfor a period no less than five years after therecord was made and shall make the recordsreadily available to the Department or theEPA upon request. [N.J.A.C. 7:27-19.11(a)]and [N.J.A.C. 7:27-19.11(b)]

None.

OS Summary

Page 126 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

2 This emergency generator shall not be used:

1. For normal testing and maintenance ondays when the Department forecasts airquality anywhere in New Jersey to be"unhealthy for sensitive groups,""unhealthy," or "very unhealthy" as definedin the EPA's Air Quality Index athttp://airnow.gov/, as supplemented oramended and incorporated herein byreference, unless required in writing by aFederal or State law or regulation.Procedures for determining the air qualityforecasts for New Jersey are available at theDepartment's air quality permitting web siteathttp://www.state.nj.us/dep/aqpp/aqforecast;and2. As a source of energy or power after theprimary energy or power source has becomeoperable again. If the primary energy orpower source is under the control of theowner or operator of the emergencygenerator, the owner or operator shall makea reasonable, timely effort to repair theprimary energy or power source. [N.J.A.C. 7:27-19.2(d)]

None. None. None.

3 NOx (Total) <= 0.535 tons/yr. Annual

emission limit based on 100 hours/year oftesting and maintenance. [N.J.A.C.7:27-22.16(a)]

None. None. None.

4 CO <= 0.117 tons/yr. Annual emission limit

based on 100 hours/year of testing andmaintenance. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

5 VOC (Total) <= 0.043 tons/yr. Annual

emission limit based on 100 hours/year oftesting and maintenance. [N.J.A.C.7:27-22.16(a)]

None. None. None.

6 SO2 <= 0.036 tons/yr. Annual emission

limit based on 100 hours/year of testing andmaintenance and 0.0015% ULSD. [N.J.A.C.7:27-22.16(a)]

None. None. None.

Page 127 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

7 TSP <= 0.038 tons/yr. Annual emission

limit based on 100 hours/year of testing andmaintenance. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

8 PM-10 (Total) <= 0.038 tons/yr. Annual

emission limit based on 100 hours/year oftesting and maintenance. [N.J.A.C.7:27-22.16(a)]

None. None. None.

9 PM-2.5 (Total) <= 0.038 tons/yr. Annual

emission limit based on 100 hours/year oftesting and maintenance. [N.J.A.C.7:27-22.16(a)]

None. None. None.

10 The owner or operator of an emergency CI

RICE <= 500 HP or black start CI RICEconstructed or reconstructed before June 12,2006 shall change oil and filter every 500hours of operation or annually, whichevercomes first, as prescribed in Table 2c, item1a to Subpart ZZZZ of 40 CFR 63. [40 CFR63.6602]

Other: The owner or operator shall changeoil and filter every 500 hours of operation orannually, whichever comes first. The owneror operator has an option of utilizing an oilanalysis program, at the same frequencyspecified for changing the oil, in order toextend the specified oil change requirement,per 40 CFR 63.6625(i). The owner oroperator must develop and follow amaintenance plan which must provide to theextent practicable for the maintenance andoperation of the engine in a mannerconsistent with good air pollution controlpractice for minimizing emissions, inaccordance with Table 6 item 9 to SubpartZZZZ of 40 CFR 63. [40 CFR 63.6640(a)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event. Theowner or operator must keep records of theoil and filter change. Each record must bereadily accessible for at least 5 years afterthe date of each occurrence, measurement,maintenance, corrective action, report, orrecord, according to 40 CFR 63.6660(c) and40 CFR 63.10(b)(1). [40 CFR63.6655(e)(2)]

None.

11 The owner or operator of an emergency CI

RICE <= 500 HP or black start CI RICEconstructed or reconstructed before June 12,2006 shall inspect air cleaner every 1,000hours of operation or annually, whichevercomes first; and inspect all hoses and beltsevery 500 hours of operation or annually,whichever comes first, and replace asnecessary, as prescribed in Table 2c, item 1band 1c to Subpart ZZZZ of 40 CFR 63. [40CFR 63.6602]

Other: The owner or operator shall inspectair cleaner every 1000 hours or annually,whichever comes first and inspect all hosesand belts every 500 hours of operation orannually, whichever comes first. The owneror operator must develop and follow amaintenance plan which must provide to theextent practicable for the maintenance andoperation of the engine in a mannerconsistent with good air pollution controlpractice for minimizing emissions, inaccordance with Table 6 item 9 to SubpartZZZZ of 40 CFR 63. [40 CFR 63.6640(a)].

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event. Theowner or operator must keep records of themaintenance procedures and air cleaner, beltand hoses replacements events. Each recordmust be readily accessible for at least 5 yearsafter the date of each occurrence,measurement, maintenance, correctiveaction, report, or record, according to 40CFR 63.6660(c) and 40 CFR 63.10(b)(1).[40 CFR 63.6655(e)(2)]

None.

Page 128 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

12 The engine must be in compliance with all

applicable emission limitations andoperating limitations in Subpart ZZZZ of 40CFR 63 at all times. [40 CFR 63.6605(a)]

None. None. None.

13 At all times the owner or operate must

operate and maintain a RICE, includingassociated air pollution control equipmentand monitoring equipment, in a mannerconsistent with safety and good air pollutioncontrol practices for minimizing emissions.[40 CFR 63.6605(b)]

None. None. None.

14 An owner or operator of an existing

stationary emergency or black start RICEmust operate and maintain the stationaryRICE and after-treatment control device (ifany) according to the manufacturer'semission-related written instructions or theowner or operator must develop amaintenance plan which must provide to theextent practicable for the maintenance andoperation of the engine in a mannerconsistent with good air pollution controlpractice for minimizing emissions. [40 CFR 63.6625(e)]

Other: Monitored according to themanufacturer's emission-related writteninstructions or the maintenance plandeveloped by the owner or operator. [40CFR 63.6625(e)].

Other: The owner or operator must keeprecords of the maintenance procedures. Eachrecord must be readily accessible for at least5 years after the date of each occurrence,measurement, maintenance, correctiveaction, report, or record, according to 40CFR 63.6660(c) and 40 CFR 63.10(b)(1).[40 CFR 63.6655(e)].

None.

15 The owner or operator must minimize the

engine's time spent at idle during startup andminimize the engine's startup time to aperiod needed for appropriate and safeloading of the engine, not to exceed 30minutes. [40 CFR 63.6625(h)]

Other: Monitored according to themanufacturer's emission-related operationand maintenance instructions; or themaintenance plan developed by the owner oroperator which must provide to the extentpracticable for the maintenance andoperation of the engine in a mannerconsistent with good air pollution controlpractice for minimizing emissions, inaccordance with Table 6 item 9 to SubpartZZZZ of 40 CFR 63. [40 CFR 63.6640(a)].

Other: The owner or operator must keeprecords of the maintenance procedures andreplacements events. Each record must bereadily accessible for at least 5 years afterthe date of each occurrence, measurement,maintenance, corrective action, report, orrecord, according to 40 CFR 63.6660(c) and40 CFR 63.10(b)(1). [40 CFR 63.6655(e)].

None.

Page 129 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

16 The owner or operator shall comply with the

General Provisions as shown in Table 8 toSubpart ZZZZ of 40 CFR 63 that apply toan existing emergency CI RICE <= 500 HPor black start RICE constructed orreconstructed before June 12, 2006 andlocated at a major source of HAP. [40 CFR63.6665]

None. None. None.

17 The owner or operator may operate an

emergency stationary RICE for the purposeof maintenance checks and readiness testing,provided that the tests are recommended byFederal, State or local government, themanufacturer, the vendor, or the insurancecompany associated with the engine.Maintenance checks and readiness testing ofsuch units is limited to 100 hours per year.The owner or operator may petition theAdministrator for approval of additionalhours to be used for maintenance checks andreadiness testing, but a petition is notrequired if the owner or operator maintainsrecords indicating that federal, state, or localstandards require maintenance and testing ofemergency RICE beyond 100 hours peryear. [40 CFR 63.6640(f)(2i)]

Monitored by hour/time monitorcontinuously. The owner or operator of anemergency stationary internal combustionengine must install a non-resettable hourmeter if one is not already installed. [40CFR 63.6625(f)]

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem annually. The owner or operatormust keep records of the hours of operationof the engine that is recorded through thenon-resettable hour meter. The owner oroperator must document how many hoursare spent for emergency operation, includingwhat classified the operation as emergencyand how many hours are spent fornon-emergency operation. If the engines areused for demand response operation, theowner or operator must keep records of thenotification of the emergency situation, andthe time the engine was operated as part ofdemand response. [40 CFR 63.6655(f)(1)]

None.

Page 130 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Emission Unit: U38 Ct 117297 - Diesel Fire PumpOperating Scenario:

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

1 Visible emissions from no greater than

20%, exclusive of condensed water vapor,except for a period of not longer than 10consecutive seconds. Opacity <= 20 %.[N.J.A.C. 7:27- 3.5]

None. None. None.

2 Maximum allowable particulate emission

rate from the combustion of fuel based onrated heat input of source. ParticulateEmissions <= 1.96 lb/hr. [N.J.A.C. 7:27-4.2(a)]

None. None. None.

3 Sulfur Content in Fuel <= 500 ppmw.

Maximum allowable sulfur content in fueloil grades/viscosity and geographical zone.(Effective through June 30, 2016). [N.J.A.C.7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery showing fuel sulfurcontent. [N.J.A.C. 7:27-22.16(o)]

None.

4 Sulfur Content in Fuel <= 15 ppmw

(0.0015% by weight). Maximum allowablesulfur content in No. 2 and lighter fuel oil.Note: This requirement is effective on andafter July 1, 2016. [N.J.A.C. 7:27- 9.2(b)]

Sulfur Content in Fuel: Monitored by reviewof fuel delivery records per delivery. Thepermittee shall check the fuel oil sulfurcontent on the invoices/bills of lading.[N.J.A.C. 7:27-22.16(o)]

Sulfur Content in Fuel: Recordkeeping byinvoices / bills of lading / certificate ofanalysis per delivery showing fuel sulfurcontent. [N.J.A.C. 7:27-22.16(o)]

None.

5 Fuel stored in New Jersey that met the

applicable maximum sulfur content standardof Tables 1A or 1B of N.J.A.C. 7:27-9.2 atthe time the fuel was stored in New Jerseymay be stored, offered for sale, sold,delivered or exchanged in trade, for use inNew Jersey, after the effective date of theapplicable standard in Table 1B. [N.J.A.C.7:27- 9.2(b)]

Monitored by review of fuel deliveryrecords upon occurrence of event and dateof storage. [N.J.A.C. 7:27-22.16(o)]

Recordkeeping by manual logging ofparameter or storing data in a computer datasystem upon occurrence of event of fuelsulfur content (ppmw or % by weight) anddate of storage. [N.J.A.C. 7:27-22.16(o)]

None.

6 This equipment shall not be used in a

manner which will cause the opacity toexceed 10%, exclusive of condensed watervapor. Opacity <= 10 %. [N.J.A.C.7:27-22.16(e)]

None. None. None.

7 Fuel use limited to distillate fuel oil.

[N.J.A.C. 7:27-22.16(e)]

None. None. None.

OS1 Detroit Diesel DDFP-06FA-8175

Page 131 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

8 Maximum emission rate from

preconstruction permit. TSP <= 0.769 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

9 Maximum Gross Heat Input <= 3.26

MMBTU/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

10 Maximum emission rate from

preconstruction permit. SO2 <= 0.717 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

13 Maximum emission rate from

preconstruction permit. CO <= 2.34 lb/hr.[N.J.A.C. 7:27-22.16(e)]

None. None. None.

12 Maximum emission rate from operating

permit application. PM-10 (Total) <= 0.769lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

11 Maximum emission rate from operating

permit application. PM-2.5 (Total) <= 0.769lb/hr. [N.J.A.C. 7:27-22.16(a)]

None. None. None.

14 Maximum emission rate from

preconstruction permit. NOx (Total) <= 10.7lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

15 Maximum emission rate from

preconstruction permit. VOC (Total) <=0.861 lb/hr. [N.J.A.C. 7:27-22.16(e)]

None. None. None.

Page 132 of 133
New Jersey Department of Environmental Protection

Facility Specific Requirements

CARNEYS POINT GENERATING PLANT (65498) BOP120002

Ref.# Applicable Requirement Monitoring Requirement Recordkeeping Requirement Su

16 Hours of Operation <= 100 hr/yr for testing

and maintenance. The limit on theallowable hours for testing and maintenancein accordance with the documentation frommanufacturer, the vendor, or the insurancecompany associated with the engine.[N.J.A.C. 7:27-22.16(a)]

Hours of Operation: Monitored by hour/timemonitor continuously. [N.J.A.C.7:27-22.16(o)]

Hours of Operation: Recordkeeping bymanual logging of parameter or storing datain a computer data system upon occurrenceof event. The owner or operator shallmaintain on site and record the followinginformation:For each time the emergency generator isspecifically operated for testing ormaintenance: i. The reason for its operation; ii. The date(s) of operation and the startup and shut down time; iii. The total operating time for testing ormaintenance based on the generator's hourmeter; and iv. The name of the operator. [N.J.A.C.7:27-19.11]

None.

Page 133 of 133
CARNEYS POINT GENERATING PLANT (65498) 

BOP120002 

New Jersey Department of Environmental Protection 

Facility Specific Requirements (Attachment #1) 

Item # 1 40 CFR 60.51Da Reporting requirements 

Subject Item: Pulv. Coal Boiler – GR2, Ref.# 53, 55, 56 

Applicable Requirement Explanation 40 CFR 60.51 Da(b) 40 CFR 60.51Da(c) 

 For sulfur dioxide and nitrogen oxides the following information is reported to the Administrator for each 24-hour p (1) Calendar dates.  (2) The average sulfur dioxide and nitrogen oxide emission rates (lb/MMBtu or lb/MW-hr) for each 30 successive 

the last 30-day period in the quarter; reasons for any noncompliance with the emission standards; and, descr

 (3) Percent reduction of the potential combustion concentration of sulfur dioxide for each 30 successive boiler ope

30-day period in the quarter; reasons for any noncompliance with the standard; and, description of corrective 

 (4) Identification of the boiler operating days for which pollutant or diluent (oxygen or carbon dioxide) data have 

method for at least 75 percent of the hours of operation of the facility; justification for not obtaining sufficiecorrective actions taken. 

(5) Identification of the times when emissions data have been excluded from the calculation of average emission 

shutdown, malfunction. 

(6) Identification of the F factor used in calculations, method of determination, and type of fuel combusted. (7) Identification of times when hourly averages have been obtained based on manual sampling methods. (8) Identification of any times when the pollutant concentration exceeded the full span of the continuous monitor

(9) Description of any modifications to the continuous monitoring system that could affect the ability of the cont

comply with Performance Specifications 2 or 3. 

If the minimum quantity of emission data as required by 40 CFR 60.49Da is not obtained for any 30 successive boileinformation obtained under the requirements of 40 CFR 60.48Da(h) is reported to the Administrator for that 30-day (1) The number of hourly averages available for outlet emission rates (no) and inlet emission rates (ni) as applica

(2) The standard deviation of hourly averages for outlet emission rates (so) and inlet emission rates (si) as applica

(3) The lower confidence limit for the mean outlet emission rate (Eo*) and the upper confidence limit for the mea

applicable. 

(4) The applicable potential combustion concentration. (5) The ratio of the upper confidence limit for the mean outlet emission rate (Eo*) and the allowable emission rat
CARNEYS POINT GENERATING PLANT (65498) 

BOP120002 

New Jersey Department of Environmental Protection 

Facility Specific Requirements (Attachment #1) 

Item # 1 40 CFR 60.51Da Reporting requirements 

Subject Item: Pulv. Coal Boiler – GR2, Ref.# 53, 55, 56 

40 CFR 60.51Da(d) 40 CFR 60.51Da(f) 40 CFR 60.51Da(h) 40 CFR 60.51Da(i) 

(d) In addition to the applicable requirements in §60.7, the owner or operator of an affected facility subject to t

conducting performance tests using Method 9 of appendix A-4 of this part shall submit excess emission reports for aaffected facility that occur during the reporting period and maintain records according to the requirements specified i

(1) For each performance test conducted using Method 9 of appendix A-4 of this part, the owner or operator sh

information specified in paragraphs (d)(1)(i) through (iii) of this section. 

(i) Dates and time intervals of all opacity observation periods; (ii) Name, affiliation, and copy of current visible emission reading certification for each visible emission obser

performance test; and 

(iii) Copies of all visible emission observer opacity field data sheets. 

 (f) For any periods for which opacity, SO2 or NOX emissions data are not available, the owner or operator of the a

signed statement indicating if any changes were made in operation of the emission control system during the period oof the control system and affected facility during periods of data unavailability are to be compared with operation of facility before and following the period of data unavailability. (h) The owner or operator of the affected facility shall submit a signed statement indicating whether: 

(1) The required CEMS calibration, span, and drift checks or other periodic audits have or have not been perfor(2) The data used to show compliance was or was not obtained in accordance with approved methods and proc

representative of plant performance. 

(3) The minimum data requirements have or have not been met; or, the minimum data requirements have not b

unavoidable. 

(4) Compliance with the standards has or has not been achieved during the reporting period. 

 (i) For the purposes of the reports required under §60.7, periods of excess emissions are defined as all 6-minute popacity exceeds the applicable opacity standards under §60.42Da(b). Opacity levels in excess of the applicable opaci

excesses are to be submitted to the Administrator each calendar quarter. 
CARNEYS POINT GENERATING PLANT (65498) Date: 10/9/2014

BOP120002

New Jersey Department of Environmental Protection

Facility Profile (General)

75

40

Long/Lat

Unknown

Other/Unknown

Other/Unknown

Rt. 130, DuPont Lacey Gate 4911 

4961 

State Plane Coordinates:

X-Coordinate:

Y-Coordinate:

Units:

Datum:

Source Org.:

Source Type:

County: Industry:

Location

Description: Primary SIC:

Secondary SIC:

Salem

Mailing

Address:

Street

Address:

500 SHELL RD

CARNEYS POINT, NJ 08069-2626

500 SHELL RD

CARNEYS POINT, NJ 08069-2626

Facility Name (AIMS): CARNEYS POINT GENERATING PLANT Facility ID (AIMS): 65498

NAICS:

Page 1 of 4
CARNEYS POINT GENERATING PLANT (65498) Date: 10/9/2014

BOP120002

New Jersey Department of Environmental Protection

Facility Profile (General)

(856) 351-6399 x 

( ) - x 

Rolf.Dinsmore@ChambersCogen.com

Chambers Cogeneration, LP

Rolf Dinsmore

Compliance Supervisor

(856) 351-6386 x Carneys Point Generating Plant

500 Shell Road

Carneys Point, NJ 08069

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: Air Permit Information Contact

(856) 351-6399 x 

( ) - x 

Rolf.Dinsmore@ChambersCogen.com

Chambers Cogeneration Limited Partnership

Rolf Dinsmore

Compliance Supervisor

(856) 351-6386 x Carneys Point Generating Station

500 Shell Road

Carneys Point, NJ 08069

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: BOP - Operating Permits

(978) 897-0099 x 

( ) - x 

ajablonowski@epsilonassociates.com

Epsilon Associates

AJ Jablonowski

Senior Engineer

(978) 461-6202 x 3 Clock Tower Place

Suite 250

Maynard, MA 01754

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Corporation

NJ EIN:

Contact Type: Consultant

Page 2 of 4
CARNEYS POINT GENERATING PLANT (65498) Date: 10/9/2014

BOP120002

New Jersey Department of Environmental Protection

Facility Profile (General)

(856) 351-6399 x 

( ) - x 

Rolf.Dinsmore@ChambersCogen.com

Chambers Cogeneration Limited Partnership

Rolf Dinsmore

Compliance Supervisor

(856) 351-6386 x Carneys Point Generating Station

500 Shell Road

Carneys Point, NJ 08069

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: Emission Statements

(856) 351-0004 x 

( ) - x 

mike.ancona@chamberscogen.com

Chambers Cogeneration Limited Partnership

Mike Ancona

Plant Manager

(856) 299-1300 x Carneys Point Generating Plant

500 Shell Road

Carneys Point, NJ 08069

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: On-Site Manager

(856) 351-0004 x 

( ) - x 

Chambers Cogeneration, LP

Steven DiCarlo

Plant Manager

(856) 299-1300 x Carneys Point Generating Plant

500 Shell Road

Carneys Point, NJ 08069

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

Partnership

NJ EIN:

Contact Type: Owner (Current CO-1)

Page 3 of 4
CARNEYS POINT GENERATING PLANT (65498) Date: 10/9/2014

BOP120002

New Jersey Department of Environmental Protection

Facility Profile (General)

(856) 351-0004 x 

(609) 619-7656 x 

sdicarlo@ppmsllc.com

Power Plant Management Services, LLC

Steve DiCarlo

General Projects Manager

(856) 376-2344 x 1 Collins Ave

Suite 100

Carneys Point, NJ 08069

Organization: Org. Type:

Name:

Title:

Phone:

Fax:

Mailing

Address:

Other:

Type:

Email:

LLC

NJ EIN:

Contact Type: Responsible Official

Page 4 of 4
CARNEYS POINT GENERATING PLANT (65498)

BOP120002

New Jersey Department of Environmental Protection

Non-Source Fugitive Emissions

FG

 NJID

Description of 

Activity Causing

Emission

Location 

Description

Reasonable Estimate of Emissions (tpy)

VOC

(Total)

NOx CO SO TSP

(Total)

PM-10 Pb H

(

FG1 Travel on Roads Facility wideFG2 Coal Handling on

Storage Pile

Storage pile

FG3 Wind Erosion from

Storage Pile

Storage pile

FG4 Miscellaneous Coal

Handling

Facility Wide

FG5 Miscellaneous Ash

Handling

Facility Wide

FG6 Miscellaneous Lime &

Dry ChemicalHandling

Faciltity Wide

Total 0.000 0.000 0.000 0.000 1.100 0.300 0.000 

Page 1 of 1
CARNEYS POINT GENERATING PLANT (65498)

BOP120002

New Jersey Department of Environmental Protection

Insignificant Source Emissions 

IS

 NJID

Source/Group

Description

Equipment Type Location 

Description

Estimate of Emissions (tpy

VOC

(Total)

NOx CO SO TSP PM-10 

IS1 Bottom ash handling (<

50 lb/hr raw materialsprocessed)

Manufacturing andMaterials HandlingEquipment

side of Boiler Bldg

IS2 Cooling Tower (< 50

lbs/hr raw materialsprocessed)

Manufacturing andMaterials HandlingEquipment

Cooling Tower

IS3 Dry Water Treatment

Chemicals (< 2000cu.ft. storage each)

Manufacturing andMaterials HandlingEquipment

Water Treat. Bldg

IS4 Magnetic Separator (<

50 lb/hr raw materialsprocessed)

Manufacturing andMaterials HandlingEquipment

Crusher Tower

IS5 Lime Grit Reject (< 50

lb/hr raw materialsprocessed)

Manufacturing andMaterials HandlingEquipment

Lime Prep. Plant

IS6 Seal Oil/ Lube Oil

Vents w/ vaporextractors (< 50 lb/hrthroughput)

Manufacturing andMaterials HandlingEquipment

plant-wide

IS7 Wastewater

Pre-treatment System(< 100 ppb for anyTXS & < 3500 ppb fortotal VOC))

Other Equipment near Water Treat.

Bldg

IS8 Boiler Water Treatment

- various steam vents (<50 lbs/hr throughput)

Boiler plant-wide

Page 1 of 2
CARNEYS POINT GENERATING PLANT (65498)

BOP120002

New Jersey Department of Environmental Protection

Insignificant Source Emissions 

IS

 NJID

Source/Group

Description

Equipment Type Location 

Description

Estimate of Emissions (tpy

VOC

(Total)

NOx CO SO TSP PM-10 

IS9 Hydrogen from steam

turbine

Other Equipment Turbine Bldg

IS10 Chemical Storage

Tanks (<= 10,000 gal,pressure < 1 atm andvapor pressure < 0.02psia)

Storage Vessel plant-wide

IS11 Parts washing (< 6 sqft,

each)

Cleaning Machine (OpenTop: Cold)

plant-wide

IS12 Plant-wide VOC use (<

50 lb/hr throughput,and < 0.5 gal/hr and <2.5 gal//day surfacecoating used)

Manufacturing andMaterials HandlingEquipment

plant-wide

IS13 Boiler cleaning (< 50

lbs/hr throughput)

Boiler Boiler Bldg

IS14 Spray Dryer Absorber

Bottom Exhaust (< 50lbs/hr throughput)

Manufacturing andMaterials HandlingEquipment

below SDA

IS15 Distillate Fuel Oil

Tanks (< 0.02 psiavapor pressure)

Storage Vessel plant-wide

IS16 Non-VOC Storage

Tanks (> 10,000 gal)

Storage Vessel plant-wide

Total 0.450 0.000 0.000 0.000 7.000 7.000 

Page 2 of 2
Equip.

NJID

Facility's 

Designation

Equipment

Description

Equipment Type Certificate

Number

Install

Date

GrandFathered L

(S

New Jersey Department of Environmental Protection

Equipment Inventory

BOP120002CARNEYS POINT GENERATING PLANT (65498) 

E1 PC Boiler 1 108170 

PCP960002

PC dry bottom boiler, 1389 No 8/2MMBtu/hr

Boiler

E2 PC Boiler 2 108169 

PCP960001

PC dry bottom boiler, 1389 No 8/2MMBtu/hr

Boiler

E3 AuxBoiler 108170 

PCP960002

Oil Fired Auxiliary Boiler, 77 No 8/2MMBtu/hr

Boiler

E4 6200CoalUnlo 115560 

PCP960006

Coal Unloader Manufacturing and No 1/6

Materials HandlingEquipment

E5 6200CoalUnlo 115560 

PCP960006

Coal Unloading Area Apron No 1/6Feeder

Manufacturing andMaterials HandlingEquipment

E6 6200CoalUnlo 115560 

PCP960006

Stack- Out Conveyor Tail Manufacturing and No 1/6

Materials HandlingEquipment

E8 6402ReclaimT 115562 

PCP960009

Reclaim Conveyor Tail Manufacturing and No 1/6

Materials HandlingEquipment

E9 6700CrusherB 099327 

PCP960008

Reclaim Belt Conveyor Head Manufacturing and No 1/6

Materials HandlingEquipment

E10 6200CoalUnlo 115560 

PCP960006

Coal Unloader Manufacturing and No 1/6

Materials HandlingEquipment

Page 1 of 4
Equip.

NJID

Facility's 

Designation

Equipment

Description

Equipment Type Certificate

Number

Install

Date

GrandFathered L

(S

New Jersey Department of Environmental Protection

Equipment Inventory

BOP120002CARNEYS POINT GENERATING PLANT (65498) 

E11 6200CoalUnlo 115560 

PCP960006

Coal Unloading Area Apron No 1/6Feeder

Manufacturing andMaterials HandlingEquipment

E12 6200CoalUnlo 115560 

PCP960006

Stack- Out Conveyor Tail Manufacturing and No 1/6

Materials HandlingEquipment

E13 6402ReclaimT 115562 

PCP960009

Reclaim Conveyor Tail Manufacturing and No 1/6

Materials HandlingEquipment

E14 6700CrusherB 099327 

PCP960008

Reclaim Belt Conveyor Head Manufacturing and No 1/6

Materials HandlingEquipment

E15 6700CrusherB 099327 

PCP960008

Coal Crusher No.1 Manufacturing and No 1/6

Materials HandlingEquipment

E16 6700CrusherB 099327 

PCP960008

Coal Crusher No.2 Manufacturing and No 1/6

Materials HandlingEquipment

E17 6700CrusherB 099327 

PCP960008

Transfer Conveyor Tail Manufacturing and No 1/6

Materials HandlingEquipment

E18 6801CoalSilo 115563 

PCP960010

Transfer Conveyor Head Manufacturing and No 1/6

Materials HandlingEquipment

E19 6801CoalSilo 115563 

PCP960010

Silo feed system: conveyor and No 1/6tripper #1

Manufacturing andMaterials HandlingEquipment

Page 2 of 4
Equip.

NJID

Facility's 

Designation

Equipment

Description

Equipment Type Certificate

Number

Install

Date

GrandFathered L

(S

New Jersey Department of Environmental Protection

Equipment Inventory

BOP120002CARNEYS POINT GENERATING PLANT (65498) 

E20 6801CoalSilo 115563 

PCP960010

Silo Feed System: Conveyor & No 1/6Tripper #2

Manufacturing andMaterials HandlingEquipment

E21 6801CoalSilo 115563 

PCP960010

Coal Silos (1) Manufacturing and No 1/6

Materials HandlingEquipment

E22 6801CoalSilo 115563 

PCP960010

Coal Silo (2) Manufacturing and No 1/6

Materials HandlingEquipment

E23 6801CoalSilo 115563 

PCP960010

Coal Silo (3) Manufacturing and No 1/6

Materials HandlingEquipment

E24 6801CoalSilo 115563 

PCP960010

Coal Silo (4) Manufacturing and No 1/6

Materials HandlingEquipment

E25 6801CoalSilo 115563 

PCP960010

Coal Silo (5) Manufacturing and No 1/6

Materials HandlingEquipment

E26 6801CoalSilo 115563 

PCP960010

Coal Silo (6) Manufacturing and No 1/6

Materials HandlingEquipment

E27 6801CoalSilo 115563 

PCP960010

Coal Silo (7) Manufacturing and No 1/6

Materials HandlingEquipment

E28 6801CoalSilo 115563 

PCP960010

Coal Silo (8) Manufacturing and No 1/6

Materials HandlingEquipment

Page 3 of 4
Equip.

NJID

Facility's 

Designation

Equipment

Description

Equipment Type Certificate

Number

Install

Date

GrandFathered L

(S

New Jersey Department of Environmental Protection

Equipment Inventory

BOP120002CARNEYS POINT GENERATING PLANT (65498) 

E29 Ash Mixer Ash Mixer Manufacturing and 8/1/2011 No 8/1

Materials HandlingEquipment

E30 5201AshTrans 115564 

PCP960012

Ash Transfer System Manufacturing and No 1/6

Materials HandlingEquipment

E34 5101AshRecyc 115558 

PCP960004

Ash Recycle Silo Manufacturing and No 1/6

Materials HandlingEquipment

E35 Ash Mixer Ash Mixer Manufacturing and 8/1/2011 No 

Materials HandlingEquipment

E36 5200AshStorS 115559 

PCP960005

Ash Storage Silo and Unloader Manufacturing and No 1/6

Materials HandlingEquipment

E37 5102LimeSlur 099322 

PCP960003

Lime Silo Manufacturing and No 1/6

Materials HandlingEquipment

E38 DetroitDiese 117297 

PCP960014

Diesel fire pump, 3.26 No 8/2MMBtu/hr

Stationary ReciprocatingEngine

Page 4 of 4
65498 CARNEYS POINT GENERATING PLANT BOP120002 E1 (Boiler) 

Print Date: 10/9/2014

PC Boiler/Natural Circulation Steam Generator

Foster Wheeler

2-78-5866

1,389.00

Field Erected

Utility

Steam Only

Wall-fired or cross-fired

Balanced





Yes

No

also firing #2 and #6 FO

Manufacturer:

Model:

Maximum Rated Gross 

Heat Input (MMBtu/hr - 

HHV):

Boiler Type:

Utility Type:

Output Type:

Steam Output (lb/hr):

Fuel Firing Method:

Description (if other):

Draft Type:

Heat Exchange Type:

Make:

Type:

Amount (%):

Is the boiler using? (check all that apply):

Have you attached a 

diagram showing the 

location and/or the 

configuration of this 

equipment?

Have you attached any 

manuf.'s data or 

specifications to aid the 

Dept. in its review of this 

application?

Comments:

Flue Gas Recirculation 

(FGR):

Low NOx Burner:

Staged Air Combustion:
65498 CARNEYS POINT GENERATING PLANT BOP120002 E2 (Boiler) 

Print Date: 10/9/2014

PC Boiler/Natural Circulation Steam Generator

Foster Wheeler

2-78-5866

1,389.00

Field Erected

Utility

Steam Only

Wall-fired or cross-fired

Balanced





Yes

No

also firing #2 and #6 FO

Manufacturer:

Model:

Maximum Rated Gross 

Heat Input (MMBtu/hr - 

HHV):

Boiler Type:

Utility Type:

Output Type:

Steam Output (lb/hr):

Fuel Firing Method:

Description (if other):

Draft Type:

Heat Exchange Type:

Make:

Type:

Amount (%):

Is the boiler using? (check all that apply):

Have you attached a 

diagram showing the 

location and/or the 

configuration of this 

equipment?

Have you attached any 

manuf.'s data or 

specifications to aid the 

Dept. in its review of this 

application?

Comments:

Flue Gas Recirculation 

(FGR):

Low NOx Burner:

Staged Air Combustion:
65498 CARNEYS POINT GENERATING PLANT BOP120002 E3 (Boiler) 

Print Date: 10/9/2014

Auxiliary Boiler

Internation Boiler Works, Inc.

WM-700R

77.00

Package

Non-Utility

Steam Only

60,000.00

Wall-fired or cross-fired

Forced

Indirect





Yes

No

Primary Fuel: No.2 Fuel Oil

Maximum Annual Fuel Use: 550,000 gal

12.00

Peabody ISC low NOx packaged burner

Manufacturer:

Model:

Maximum Rated Gross 

Heat Input (MMBtu/hr - 

HHV):

Boiler Type:

Utility Type:

Output Type:

Steam Output (lb/hr):

Fuel Firing Method:

Description (if other):

Draft Type:

Heat Exchange Type:

Make:

Type:

Amount (%):

Is the boiler using? (check all that apply):

Have you attached a 

diagram showing the 

location and/or the 

configuration of this 

equipment?

Have you attached any 

manuf.'s data or 

specifications to aid the 

Dept. in its review of this 

application?

Comments:

Flue Gas Recirculation 

(FGR):

Low NOx Burner:

Staged Air Combustion:
65498 CARNEYS POINT GENERATING PLANT BOP120002 E4 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Coal Unloader

1.40E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal: 800 hrs/yr, 8 hrs/batch

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E5 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Coal Unloading Area Apron Feeder

1.40E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal: 800 hrs/yr, 8 hrs/batch

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E6 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Stack-Out Conveyor Tail

1.40E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal: 800 hrs/yr, 8 hrs/batch

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E8 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Reclaim Conveyor Tail

5.00E+06

other units

lb/batch

Yes

No

Make:

Bituminous coal: 1800 hrs/yr, 5 hrs/batch

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E9 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Reclaim Conveyor Head

5.00E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal - 1800 hrs/yr, 5 hrs/batch

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E10 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Coal Unloader

5.00E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal: 900,000 tons/yr, 1,030 hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E11 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Coal Unloading Area Apron Feeder

5.00E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal: 900,000 tons per year,

1,030 hrs/yr;

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E12 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Transfer Conveyor Tail

5.00E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal - 1800 hrs/yr, 5 hrs/batch

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E13 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Reclaim Conveyor Tail

5.00E+06

other units

lbs/batch

Yes

No

Make:

Bituminous coal: 900,000 tons/yr, 1800 hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E14 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Reclaim Conveyor Head

5.00E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E15 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Crusher

5.00E+06

other units

lbs/batch

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E16 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Crusher

other units

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E17 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Transfer Conveyor Tail

other units

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E18 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Transfer Conveyor Head

other units

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E19 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Silo Feed Conveyor and Tripper

other units

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E20 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Silo Feed Conveyor and Tripper

other units

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E21 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

ft^3

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E22 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

ft^3

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E23 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

ft^3

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E24 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

9.00E+05

ft^3

lbs/ batch

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E25 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

ft^3

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E26 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

5.60E+04

ft^3

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E27 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

3.62E+04

ft^3

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E28 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Bituminous Coal Storage Silo

ft^3

Yes

No

Make:

Bituminous Coal - 900,000 tons/yr, 1800

hrs/yr

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E29 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Mixer Systems or Equivalent

Mixer Systems or Equivalent

Dustmaster ash mixing system or equivalent

Ash mixer

3.00E+03

gallons

No

No

Make:

The ash mixer will condition the flyash by

mixing it with water. This will allow additional

transport and disposal options.

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E30 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Ash Transfer System

other units

Yes

No

Make:

Fly Ash & SO2 Scrubber Waste - 3560 hrs/yr,

Annual limit of of ash transferred from PC

boiler's baghouse to ash storage silo. Total

Material Transferred <= 160,200 tons/yr.

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E34 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Ash Recycle Silo

ft^3

Yes

No

Make:

Continuous transfer of Fly Ash & SO2

Scrubber Waste to Ash Recycle Silo - Annual

limit of ash transferred to ash recycle silo.

Total Material Transferred <= 35,040 tons/yr.

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E35 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Mixer Systems or Equivalent

Mixer Systems or Equivalent

Dustmaster ash mixing system or equivalent

Ash mixer

gallons

No

No

Make:

The ash mixer will condition the flyash by

mixing it with water. This will allow additional

transport and disposal options.

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E36 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Ash Storage Silo & Unloader

ft^3

Yes

No

Make:

Fly ash & SO2 Scrubber Waste - 1600 hrs/yr,

Annual limit of ash transferred from silo to

enclosed rail cars. Total Material Transferred

<= 160,200 tons/yr.

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E37 (Manufacturing and Materials Handling Equipment) 

Print Date: 10/9/2014

Silo Filling

ft^3

No

No

Make:

2000 hr/yr, Annual limit of pebble lime

throughput. Total Material Transferred <=

80,000 tons/yr.

Have you attached any manuf.'s 

data or specifications to aid the 

Dept. in its review of this 

application?

Description (if other):

Units:

Capacity:

Type of Manufacturing and Materials 

Handling Equipment:

Model:

Manufacturer:

Comments:

Have you attached a diagram 

showing the location and/or the 

configuration of this equipment?
65498 CARNEYS POINT GENERATING PLANT BOP120002 E38 (Stationary Reciprocating Engine)

Print Date: 10/9/2014

Make:

Manufacturer: Detroit Diesel

Model: DDFP-06FA-8175

Maximum Rated Gross Heat

Input (MMBtu/hr):

3.26

Class: Diesel

Duty: emergency fire pump

Description:

Load Range (%):

Stroke:

Power Output (BHP): 412

Electric Output (KW):

Compression Ratio:

Ignition Type:

Engine Speed (RPM):

Engine Exhaust Temperature

(deg F):

Air to Fuel Ratio at Peak Load:

Lambda Factor (scfm/scfm):

Brake Specific Fuel

Consumption at Peak Load

(Btu/BHP-hr):

Output Type:

Heat to Power Ratio:

Is the Engine Using a

Turbocharger?

Is the Engine Using an

Aftercooler?

No

Is the Engine Using (check all

that apply):

A Prestratified Charge (PSC)
65498 CARNEYS POINT GENERATING PLANT BOP120002 E38 (Stationary Reciprocating Engine)

Print Date: 10/9/2014

A NOx Converter

Air to Fuel Adjustment (AF)

 Ignition Timing Retard

Low Emission Combustion

Non-Selective Catalytic Retard

(NSCR)

Other

Description:

Have you attached a diagram

showing the location and/or

configuration of this

equipment?

Yes

Have you attached any

manufacturer’s data or

specifications which may aid

in the review of this

application?

No

Comments: distillate fuel (0.2% sulfur in fuel)

Include Emission Rates on the Potential to Emit Screen for each 

Contaminant in grams/BHP-hr and ppmdv @7% O2 in addition

to lbs/hr and tons/yr.
CARNEYS POINT GENERATING PLANT (65498) Da

New Jersey Department of Environmental Protection

Control Device Inventory

CD

 NJID

Facility's 

Designation

Description CD Type Install

Date

GrandFathered Last Mod. (Since 1968) 

BOP120002

CD1 Selective Catalytic Reduction for

PC Boiler 1

PC Boiler 1 Selective Catalytic No

Reduction

CD2 Spray Dryer Absorber for PC

Boiler 1

PC Boiler 1 Scrubber (Other) No

CD3 PC Boiler 1 Baghouse for PC Boiler 1 Particulate Filter No

(Baghouse)

CD4 Selective Catalytic Reduction for

PC Boiler 2

PC Boiler 2 Selective Catalytic No

Reduction

CD5 Spray Dryer Absorber for PC

Boiler 2

PC Boiler 2 Scrubber (Other) No

CD6 PC Boiler 2 Baghouse for PC Boiler 2 Particulate Filter No

(Baghouse)

CD8 Fabric Filter: Coal Unloading

Area

6200CoalUnlo Particulate Filter No

(Baghouse)

CD11 Fabric Filter: Coal Unloading

Area

6200CoalUnlo Particulate Filter No

(Baghouse)

CD12 6700CrusherB Fabric Filter : Crusher Building Particulate Filter No

(Baghouse)

CD13 Fabric Filter: Coal Reclaim

Conveyor Tail

6402ReclaimT Particulate Filter No

(Baghouse)

CD14 6700CrusherB Fabric Filter : Crusher Building Particulate Filter No

(Baghouse)

CD15 5101AshRecyc Fabric Filter : Ash Recycle Silo Particulate Filter No

(Baghouse)

Page 1 of 2
CARNEYS POINT GENERATING PLANT (65498) Da

New Jersey Department of Environmental Protection

Control Device Inventory

CD

 NJID

Facility's 

Designation

Description CD Type Install

Date

GrandFathered Last Mod. (Since 1968) 

BOP120002

CD16 5200AshStorS Fabric Filter: Ash Storage Silo Particulate Filter No

(Baghouse)

CD17 5102LimeSlur Fabric Filter: Lime Silo Particulate Filter No

(Baghouse)

CD18 6801CoalSilo Fabric Filter : Coal Silo Bay Particulate Filter 8/1/2011 No 8/1/2011

(Baghouse)

CD30 Fabric Filter: Ash Transfer

System

5201AshTrans Particulate Filter No

(Baghouse)

CD34 5101AshRecyc Fabric Filter : Ash Recycle Silo Particulate Filter No

(Baghouse)

CD35 AshMix Filt Fabric Filter: Ash Mixer Particulate Filter 8/1/2011 No 8/1/2011

(Cartridge)

CD36 5200AshStorS Fabric Filter: Ash Storage Silo Particulate Filter No

(Baghouse)

CD37 5102LimeSlur Fabric Filter: Lime Silo Particulate Filter No

(Baghouse)

Page 2 of 2
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD1 (Selective Catalytic Reduction)

Print Date: 10/9/2014

Make:

Manufacturer: Ishikawajima - Harima

Model:

Minimum Temperature at

Catalyst Bed (deg F):

Maximum Temperature at

Catalyst Bed (deg F):

Minimum Temperature at

Reagent Injection Point (deg

F):

Maximum Temperature at

Reagent Injection Point (deg

F):

Type of Reagent: Ammonia, Aqueous < 28%

Chemical Formula of

Reagent:

NH3

Minimum Reagent Charge

Rate (gpm):

300gpm

Maximum Reagent Charge

Rate (gpm):

400gpm

Minimum Concentration of

Reagent in Solution (%

Volume):

Minimum NOx to Reagent

Mole Ratio:

Maximum NOx to Reagent

Mole Ratio:

Maximum Anticipated

Ammonia Slip (ppm):

5 ppmvd @ 7% O2

Type of Catalyst: Honeycomb

Volume of Catalyst (ft3): 163.3 m3 for each two layers

Form of Catalyst: TiO2 - V205

Anticipated Life of Catalyst: 61,000 - 87,600

Units: hours

Have you attached a catalyst

replacement schedule?

No
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD1 (Selective Catalytic Reduction)

Print Date: 10/9/2014

Method of Determining

Breakthrough:

CEMS, Ammonia Slip

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

1

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

No

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Yes

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD1 (Selective Catalytic Reduction)

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD3 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2 ):

Total Bag Area (ft2):

Bag Fabric:

Fabric Weight (oz/ft):

Fabric Weave:

Fabric Finish:

Maximum Design

Temperature Capability (deg

F):

Maximum Design Air Flow

Rate (acfm):

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

Minimum Operating

Pressure Drop (in. H2O):

3

Maximum Operating

Pressure Drop (in. H2O):

12

Method of Monitoring

Pressure Drop:

Maximum Inlet Temperature

(deg F):

Minimum Inlet Temperature

(deg F):

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

Maximum Inlet Gas Stream

Moisture Content (%):
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD3 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Method for Determining

When Cleaning is Required:

Method of Bag Cleaning:

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD3 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD6 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2 ):

Total Bag Area (ft2):

Bag Fabric:

Fabric Weight (oz/ft):

Fabric Weave:

Fabric Finish:

Maximum Design

Temperature Capability (deg

F):

Maximum Design Air Flow

Rate (acfm):

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

Minimum Operating

Pressure Drop (in. H2O):

Maximum Operating

Pressure Drop (in. H2O):

~12

Method of Monitoring

Pressure Drop:

Maximum Inlet Temperature

(deg F):

Minimum Inlet Temperature

(deg F):

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

Maximum Inlet Gas Stream

Moisture Content (%):
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD6 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Method for Determining

When Cleaning is Required:

Method of Bag Cleaning:

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD6 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD8 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make: Fabric Filter : Coal Unloading Area

Manufacturer:

Model:

Number of Bags: 81

Size of Bags (ft2 ): 9.25" diam. X 121 " long 

Total Bag Area (ft2): 1256

Bag Fabric: Singed Dacron Polyester 

Fabric Weight (oz/ft): 16

Fabric Weave: Normal

Fabric Finish: Singed

Maximum Design

Temperature Capability (deg

F):

275

Maximum Design Air Flow

Rate (acfm):

10000

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

5.6:1

Minimum Operating

Pressure Drop (in. H2O):

1.5

Maximum Operating

Pressure Drop (in. H2O):

9

Method of Monitoring

Pressure Drop:

 Magnehellic differential pressure gauge

Maximum Inlet Temperature

(deg F):

Ambient 

Minimum Inlet Temperature

(deg F):

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

7500

Maximum Inlet Gas Stream

Moisture Content (%):

Ambient 
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD8 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Pulse Jet on high pressure drop 

Method for Determining

When Cleaning is Required:

same as above 

Method of Bag Cleaning: Pulse Jet 

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

2

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD8 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD11 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Fabric Filter: Coal Unloading Area

Dacron felt or equivalent

Magnehellic differential pressure gauge

5.00

1.50

9.00

7,500.0

16.00

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2):

Total Bag Area (ft2):

Dew Point of Gas Stream Maximum 

Inlet Temperature (°F):

Maximum Air Flow Rate to Cloth Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Minimum Inlet Temperature (°F):

Maximum Inlet Temperature (°F):

Maximum Operating Pressure Drop (in. H2O):

Method of Monitoring Pressure Drop:

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Maximum Inlet Gas Stream Moisture 

Content (%):

Draft Type:

Bag Fabric:

Fabric Weight (oz/ft2):

Maximum Design Temperature Capability (°F):

Fabric Weave:

Fabric Finish:

Maximum Design Air Flow Rate (acfm):

Method for Determining When Bag 

Replacement is Required:

Have you attached a Particle Size 

Distribution Analysis? Yes No

2

Method of Bag Cleaning:

Description:

Is Bag Cleaning Conducted On-Line?

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Yes No

Pulse Jet

Method for Determining When Cleaning

is Required:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD11 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD12 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make: Fabric Filter: Crusher Building 

Manufacturer:

Model:

Number of Bags: 153

Size of Bags (ft2 ): 9.25" dia X 121" long 

Total Bag Area (ft2): 2372

Bag Fabric: Singed Dacron Polyester

Fabric Weight (oz/ft): 16

Fabric Weave: normal 

Fabric Finish: singed

Maximum Design

Temperature Capability (deg

F):

275

Maximum Design Air Flow

Rate (acfm):

10000

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

6.1:1

Minimum Operating

Pressure Drop (in. H2O):

1.5

Maximum Operating

Pressure Drop (in. H2O):

9

Method of Monitoring

Pressure Drop:

Magnehellic differential pressure gauge

Maximum Inlet Temperature

(deg F):

Ambient 

Minimum Inlet Temperature

(deg F):

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

7500

Maximum Inlet Gas Stream

Moisture Content (%):

ambient 
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD12 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Pulse jet on high pressure drop

Method for Determining

When Cleaning is Required:

same as above

Method of Bag Cleaning: Pulse Jet 

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

4

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD12 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD13 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Fabric Filter: Coal Reclaim Conveyor Tail

Dacron felt or equivalent

Magnehelic differential pressure gauge

5.00

3.00

9.00

7,500.0

16.00

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2):

Total Bag Area (ft2):

Dew Point of Gas Stream Maximum 

Inlet Temperature (°F):

Maximum Air Flow Rate to Cloth Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Minimum Inlet Temperature (°F):

Maximum Inlet Temperature (°F):

Maximum Operating Pressure Drop (in. H2O):

Method of Monitoring Pressure Drop:

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Maximum Inlet Gas Stream Moisture 

Content (%):

Draft Type:

Bag Fabric:

Fabric Weight (oz/ft2):

Maximum Design Temperature Capability (°F):

Fabric Weave:

Fabric Finish:

Maximum Design Air Flow Rate (acfm):

Method for Determining When Bag 

Replacement is Required:

Have you attached a Particle Size 

Distribution Analysis? Yes No

1

Method of Bag Cleaning:

Description:

Is Bag Cleaning Conducted On-Line?

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Yes No

Pulse Jet

Method for Determining When Cleaning

is Required:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD13 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD14 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Fabric Filter: Crusher Building

504

Dacron felt or equivalent

Magnehelic differential pressure gauge

5.00

1.50

9.00

7,500.0

16.00

Normal

Normal

12,200.0

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2):

Total Bag Area (ft2):

Dew Point of Gas Stream Maximum 

Inlet Temperature (°F):

Maximum Air Flow Rate to Cloth Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Minimum Inlet Temperature (°F):

Maximum Inlet Temperature (°F):

Maximum Operating Pressure Drop (in. H2O):

Method of Monitoring Pressure Drop:

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Maximum Inlet Gas Stream Moisture 

Content (%):

Draft Type:

Bag Fabric:

Fabric Weight (oz/ft2):

Maximum Design Temperature Capability (°F):

Fabric Weave:

Fabric Finish:

Maximum Design Air Flow Rate (acfm):

Method for Determining When Bag 

Replacement is Required:

Pulse jet on high pressure drop

Have you attached a Particle Size 

Distribution Analysis? Yes No

4

Method of Bag Cleaning:

Description:

Is Bag Cleaning Conducted On-Line?

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Yes No

Pulse Jet

Method for Determining When Cleaning

is Required:

Same as above

120.0

5,120.0
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD14 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

There are 4 housings with 126 bags per housing.

The size of each bag is 84". The total bag area is

1280 ft2 per housing. The inlet gas stream moisture

content will be equal to ambient moisture.

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD15 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make: Fabric Filter : Ash Recycle Silo 

Manufacturer:

Model:

Number of Bags: 130

Size of Bags (ft2 ): 6" dia X 10' Long 

Total Bag Area (ft2): 2035

Bag Fabric: Dacron Felt

Fabric Weight (oz/ft): 16

Fabric Weave: Normal

Fabric Finish: Normal

Maximum Design

Temperature Capability (deg

F):

275

Maximum Design Air Flow

Rate (acfm):

10000

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

5.0:1

Minimum Operating

Pressure Drop (in. H2O):

3

Maximum Operating

Pressure Drop (in. H2O):

9

Method of Monitoring

Pressure Drop:

Maximum Inlet Temperature

(deg F):

Minimum Inlet Temperature

(deg F):

120

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

7500

Maximum Inlet Gas Stream

Moisture Content (%):

Ambient 
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD15 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Pulse Jet on timer 

Method for Determining

When Cleaning is Required:

same as above 

Method of Bag Cleaning: pulse jet 

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

1

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD15 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD16 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make: Fabric Filter: Ash Storage Silo

Manufacturer:

Model:

Number of Bags: 8

Size of Bags (ft2 ): 120 in

Total Bag Area (ft2): 1312

Bag Fabric: Polyester (plain)

Fabric Weight (oz/ft): 16

Fabric Weave: Normal 

Fabric Finish: Normal

Maximum Design

Temperature Capability (deg

F):

450

Maximum Design Air Flow

Rate (acfm):

3000

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

2.3:1

Minimum Operating

Pressure Drop (in. H2O):

0.5

Maximum Operating

Pressure Drop (in. H2O):

9

Method of Monitoring

Pressure Drop:

Magnehelic differential pressure gauge

Maximum Inlet Temperature

(deg F):

Minimum Inlet Temperature

(deg F):

200

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

2250

Maximum Inlet Gas Stream

Moisture Content (%):

Ambient 
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD16 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Method for Determining

When Cleaning is Required:

Method of Bag Cleaning: Pulse Jet 

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

1

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD16 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD17 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Fabric Filter: Lime Silo

40

Dacron Felt

Magnahelic Differential Pressure Gauge

5.00

100.0

3.00

9.00

2,500.0

16.00

Normal (singed)

Normal

275.0

2,500.0

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2):

Total Bag Area (ft2):

Dew Point of Gas Stream Maximum 

Inlet Temperature (°F):

Maximum Air Flow Rate to Cloth Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Minimum Inlet Temperature (°F):

Maximum Inlet Temperature (°F):

Maximum Operating Pressure Drop (in. H2O):

Method of Monitoring Pressure Drop:

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Maximum Inlet Gas Stream Moisture 

Content (%):

Draft Type:

Bag Fabric:

Fabric Weight (oz/ft2):

Maximum Design Temperature Capability (°F):

Fabric Weave:

Fabric Finish:

Maximum Design Air Flow Rate (acfm):

Method for Determining When Bag 

Replacement is Required:

Pulse on high pressure drop

Have you attached a Particle Size 

Distribution Analysis? Yes No

1

Method of Bag Cleaning:

Description:

Is Bag Cleaning Conducted On-Line?

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Yes No

Pulse Jet

Method for Determining When Cleaning

is Required:

Same as above

10.0

12.50

500.0
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD17 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD18 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Cartridge Filter or equivalent

Dustmaster or equivalent

850 CFM cartridge filter or equivalent

6

3.75

500.0

0.01

20.00

1,000.0

500.0

1,000.0

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2):

Total Bag Area (ft2):

Dew Point of Gas Stream Maximum 

Inlet Temperature (°F):

Maximum Air Flow Rate to Cloth Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Minimum Inlet Temperature (°F):

Maximum Inlet Temperature (°F):

Maximum Operating Pressure Drop (in. H2O):

Method of Monitoring Pressure Drop:

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Maximum Inlet Gas Stream Moisture 

Content (%):

Draft Type:

Bag Fabric:

Fabric Weight (oz/ft2):

Maximum Design Temperature Capability (°F):

Fabric Weave:

Fabric Finish:

Maximum Design Air Flow Rate (acfm):

Method for Determining When Bag 

Replacement is Required:

annual inpsection

Have you attached a Particle Size 

Distribution Analysis? Yes No

1

Method of Bag Cleaning:

Description:

Is Bag Cleaning Conducted On-Line?

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Yes No

Visual inspection once per shift during site 

walk-throughs

Method for Determining When Cleaning

is Required:

44.50

267.0
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD18 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Design and operating parameters are approximate

and not to be considered permit limits.

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD18 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make: Fabric Filter: Coal Silo Bay

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2 ):

Total Bag Area (ft2):

Bag Fabric: Dacron felt or equivalent

Fabric Weight (oz/ft): 16

Fabric Weave:

Fabric Finish:

Maximum Design

Temperature Capability (deg

F):

Maximum Design Air Flow

Rate (acfm):

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

5

Minimum Operating

Pressure Drop (in. H2O):

3

Maximum Operating

Pressure Drop (in. H2O):

9

Method of Monitoring

Pressure Drop:

Magnehellic differntial pressure guage

Maximum Inlet Temperature

(deg F):

Minimum Inlet Temperature

(deg F):

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

15000

Maximum Inlet Gas Stream

Moisture Content (%):
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD18 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Method for Determining

When Cleaning is Required:

Method of Bag Cleaning: pulse jet 

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD18 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD30 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Fabric Filter: Ash Transfer System

Nomex or equivalent

differential pressure gauge

5.10

120.0

9,900.0

14.00

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2):

Total Bag Area (ft2):

Dew Point of Gas Stream Maximum 

Inlet Temperature (°F):

Maximum Air Flow Rate to Cloth Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Minimum Inlet Temperature (°F):

Maximum Inlet Temperature (°F):

Maximum Operating Pressure Drop (in. H2O):

Method of Monitoring Pressure Drop:

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Maximum Inlet Gas Stream Moisture 

Content (%):

Draft Type:

Bag Fabric:

Fabric Weight (oz/ft2):

Maximum Design Temperature Capability (°F):

Fabric Weave:

Fabric Finish:

Maximum Design Air Flow Rate (acfm):

Method for Determining When Bag 

Replacement is Required:

Have you attached a Particle Size 

Distribution Analysis? Yes No

Method of Bag Cleaning:

Description:

Is Bag Cleaning Conducted On-Line?

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Yes No

Pulse Jet

Method for Determining When Cleaning

is Required:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD30 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD34 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make: Fabric Filter : Ash Recycle Silo 

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2 ):

Total Bag Area (ft2):

Bag Fabric: Dacron felt or equivalent

Fabric Weight (oz/ft): 16

Fabric Weave:

Fabric Finish:

Maximum Design

Temperature Capability (deg

F):

Maximum Design Air Flow

Rate (acfm):

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

5.0:1

Minimum Operating

Pressure Drop (in. H2O):

3

Maximum Operating

Pressure Drop (in. H2O):

9

Method of Monitoring

Pressure Drop:

Maximum Inlet Temperature

(deg F):

Minimum Inlet Temperature

(deg F):

120

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

7500

Maximum Inlet Gas Stream

Moisture Content (%):
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD34 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Method for Determining

When Cleaning is Required:

Method of Bag Cleaning: pulse jet 

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

1

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD34 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD35 (Particulate Filter (Cartridge)) 

Print Date: 10/9/2014

Cartridge Filter or equivalent

Dustmaster or equivalent

850 CFM cartridge filter or equivalent

6

44.50

267.00

500.0

1,000.0

3.75

0.01

20.00

500.0

1,000.0

annual inspection

Make:

Manufacturer:

Model:

Number of Cartridges:

Size of Cartridges (ft2):

Total Cartridge Area (ft2):

Maximum Design Temperature Capability (°F):

Maximum Design Air Flow Rate (acfm):

Maximum Air Flow Rate to Filter Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Maximum Operating Pressure Drop (in. H2O):

Maximum Inlet Temperature (°F):

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Method for Determining When Cartridge

Replacement is Required:

Design and operating parameters are approximate

and not to be considered permit limits.

Have you attached a Particle Size 

Distribution Analysis?

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No

Yes No

1

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Visual inspection once per shift during site

walk-throughs
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD36 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Make: Fabric Filter: Ash Storage Silo

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2 ):

Total Bag Area (ft2):

Bag Fabric: Nomex or equivalent

Fabric Weight (oz/ft): 16

Fabric Weave:

Fabric Finish:

Maximum Design

Temperature Capability (deg

F):

Maximum Design Air Flow

Rate (acfm):

Draft Type:

Maximum Air Flow Rate to

Cloth Area Ratio:

2.5:1

Minimum Operating

Pressure Drop (in. H2O):

0.5

Maximum Operating

Pressure Drop (in. H2O):

9

Method of Monitoring

Pressure Drop:

Magnehelic differential pressure gauge

Maximum Inlet Temperature

(deg F):

200

Minimum Inlet Temperature

(deg F):

Dew Point of Gas Stream

(deg F):

Maximum Operating Exhaust

Gas Flow Rate (acfm):

2250

Maximum Inlet Gas Stream

Moisture Content (%):
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD36 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Method for Determining

When Bag Replacement is

Required:

Method for Determining

When Cleaning is Required:

Method of Bag Cleaning: Pulse Jet 

Is Bag Cleaning Conducted

On-Line?

Maximum Number of

Sources Using this

Apparatus as a Control

Device (Include Permitted

and Non-permitted Sources):

1

Alternative Method to

Demonstrate Control

Apparatus is Operating

Properly:

Have you attached a Particle

Size Distribution Analysis?

Have you attached data from

recent performance testing?

Have you attached any

manufacturer’s data or

specifications in support of

the feasibility and/or

effectiveness of this control

apparatus?

Have you attached a diagram

showing the location and/or

configuration of this control

apparatus?

Comments:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD36 (Particulate Filter (Baghouse))

Print Date: 10/9/2014

Control Device Design Efficiency Table

Pollutant Category Design Efficiency (%)

PM-10

TSP

VOC

NOx

SO2

CO

Pb

HAPs (Total)

Other (Total)

Individual HAPs/Other

(speciate below)
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD37 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Fabric Filter: Lime Silo

Dacron felt or equivalent

Magnehellic differential pressure gauge

5.00

3.00

9.00

2,500.0

16.00

Make:

Manufacturer:

Model:

Number of Bags:

Size of Bags (ft2):

Total Bag Area (ft2):

Dew Point of Gas Stream Maximum 

Inlet Temperature (°F):

Maximum Air Flow Rate to Cloth Area Ratio:

Minimum Operating Pressure Drop (in. H2O):

Minimum Inlet Temperature (°F):

Maximum Inlet Temperature (°F):

Maximum Operating Pressure Drop (in. H2O):

Method of Monitoring Pressure Drop:

Maximum Operating Exhuast Gas Flow 

Rate (acfm):

Maximum Inlet Gas Stream Moisture 

Content (%):

Draft Type:

Bag Fabric:

Fabric Weight (oz/ft2):

Maximum Design Temperature Capability (°F):

Fabric Weave:

Fabric Finish:

Maximum Design Air Flow Rate (acfm):

Method for Determining When Bag 

Replacement is Required:

Have you attached a Particle Size 

Distribution Analysis? Yes No

1

Method of Bag Cleaning:

Description:

Is Bag Cleaning Conducted On-Line?

Maximum Number of Sources Using

this Apparatus as a Control Device 

(Include Permitted and 

Non-Permitted Sources):

Alternative Method to Demonstrate 

Control Apparatus is Operating 

Properly:

Yes No

Pulse Jet

Method for Determining When Cleaning

is Required:
65498 CARNEYS POINT GENERATING PLANT BOP120002 CD37 (Particulate Filter (Baghouse)) 

Print Date: 10/9/2014

Have you attached data from recent

performance testing?

Comments:

Have you attached any 

manufacturer's data or specifications 

in support of the feasibility and/or 

effectiveness of this control 

apparatus?

Have you attached a diagram 

showing the location and/or 

configuration of this control 

apparatus? Yes No

Yes No

Yes No
CARNEYS POINT GENERATING PLANT (65498) 

New Jersey Department of Environmental Protection

Emission Points Inventory

PT

 NJID

Facility's 

Designation

Description Config. Equiv.

Diam.

(in.)

Height

(ft.)

Dist. to

Prop.

Line (ft)

Exhaust Temp. (deg. F) Exhaust V

Avg. Min. Max. Avg. Mi

BOP120002

PT1 PC Boiler 1 and Aux Boiler Round 126 475 110 100.0 300.0 30PT2 PC Boiler 2 Round 126 475 110 100.0 300.0 30PT3 Coal Unloading Roof Vent 30 35 350 10.0 100.0 10PT4 Coal Unload Area Rectangle 20 10 450 10.0 100.0 5PT6 Reclaim Conv. Tail Rectangle 20 30 150 10.0 100.0 5PT7 Crusher Building Rectangle 20 80 250 10.0 100.0 5PT8 Coal Silo Bay Rectangle 20 180 250 10.0 100.0 10PT10 Coal Unloading Roof Vent Round 30 35 350 10.0 100.0 10PT11 Coal Unload Area Rectangle 20 10 450 10.0 100.0 5PT12 Lime Silo Rectangle 5 90 225 10.0 100.0 1PT13 Reclaim Conv. Tail Rectangle 20 30 150 10.0 100.0 5PT14 Crusher Building Rectangle 20 80 250 10.0 100.0 5PT15 Ash Transfer System Rectangle 10 80 165 10.0 200.0 1PT16 Ash Transfer System Rectangle 10 80 165 10.0 200.0 1PT17 Ash Transfer System Rectangle 10 80 165 10.0 200.0 1PT18 AshMix vent Coal Silo Bay Rectangle 20 180 250 120.0 10.0 100.0 850.0 10PT30 Ash Transfer System Rectangle 10 80 165 10.0 200.0 1PT31 Ash Transfer System Rectangle 10 80 165 10.0 200.0 1PT32 Ash Transfer System Rectangle 10 80 165 10.0 200.0 1

Page 1 of 2
CARNEYS POINT GENERATING PLANT (65498) 

New Jersey Department of Environmental Protection

Emission Points Inventory

PT

 NJID

Facility's 

Designation

Description Config. Equiv.

Diam.

(in.)

Height

(ft.)

Dist. to

Prop.

Line (ft)

Exhaust Temp. (deg. F) Exhaust V

Avg. Min. Max. Avg. Mi

BOP120002

PT33 Ash Transfer System Rectangle 10 80 165 10.0 200.0 1PT34 Ash Recycle Silo Round 12 50 200 10.0 150.0 5PT35 AshMix Vent Ash Mixer Vent Round 7 25 300 120.0 0.0 500.0 850.0 PT36 Ash Storage Silo Rectangle 24 180 80 10.0 100.0 1PT37 Lime Silo Rectangle 5 90 225 10.0 100.0 1PT38 Diesel Fire Pump Round 6 25 350 200.0 1,000.0 

Page 2 of 2
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 1 PC#1 Ct 108170 - PC Boiler #1

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 CoaBoil1 PC Boiler 1: Normal

Firing using coal and/orNo. 2 and/or No. 6 oil

Normal - SteadyState

E1 CD1 (P)

CD2 (S)CD3 (T)

PT1 1-01-005-01 

1-01-002-02 1-01-002-01 

OS2 S/U Boiler1 PC Boiler #1: Start-up Startup E1 CD1 (P)

CD2 (S)CD3 (T)

PT1 1-01-005-01 

OS3 S/D Boiler1 PC Boiler #1: Shut-down Shutdown E1 PT1 U 2 PC#2 Ct 108169 - PC Boiler #2

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 CoaBoil2 PC Boiler 2: Normal firing

using coal and/or No. 2 oiland/or No. 6 oil

Normal - SteadyState

E2 CD4 (P)

CD5 (S)CD6 (T)

PT2 1-01-005-01 

1-01-002-02 

OS2 S/U Boiler2 PC Boiler 2: Start-up Startup E2 CD4 (P)

CD5 (S)CD6 (T)

PT2 1-01-005-01 

OS3 S/D Boiler2 PC Boiler 2: Shutdown Shutdown E2 PT2 

Page 1 of 8
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 3 Aux Boil Auxiliary Boiler

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 Aux Boil Auxiliary Boiler Normal

Operation

Normal - SteadyState

E3 PT1 

PT3 

1-03-005-02 3-05-010-11 

1,000.0

OS2 S/U Aux Boil Auxiliary Boiler: Start-up Startup E3 PT1 1-03-005-02 OS3 S/D Aux Boil Auxiliary Boiler:

Shutdown

Shutdown E3 PT1 1-03-005-02 

U 10 6200CoalUnlo Ct 115560 - Coal Unloader

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 6200CoalUnlo Coal Unloader Normal - Steady

State

E10 PT10 3-05-010-11 800.0

Page 2 of 8
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 11 6200CoalUnlo Ct 115560 - Apron Feeder & Stack-out Conveyor Tail

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 6200CoalUnlo Coal Unloading Apron

Feeder

Normal - SteadyState

E11 CD11 (P) PT11 3-05-010-11 800.0

OS2 6200CoalUnlo Stack-out Conveyor Tail Normal - Steady

State

E12 CD11 (P) PT11 3-05-010-11 800.0

U 13 6402ReclaimT Ct 115562 - Reclaim Conveyor Tail

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 6402ReclaimT Reclaim Conveyor Tail Normal - Steady

State

E13 CD13 (P) PT13 3-05-010-11 1,800.0

Page 3 of 8
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 14 6700CrusherB Ct 099327 - 6700 Crusher Bldg. Baghouse.

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 6700CrusherB Reclaim Conveyor Head Normal - Steady

State

E14 CD14 (P) PT14 3-05-010-11 1,800.0

OS2 6700CrusherB Crusher No. 1 Normal - Steady

State

E15 CD14 (P) PT14 3-05-010-10 1,800.0

OS3 6700CrusherB Crusher No.2 Normal - Steady

State

E16 CD14 (P) PT14 3-05-010-10 1,800.0

OS4 6700CrusherB Transfer Conveyor Tail Normal - Steady

State

E17 CD14 (P) PT14 3-05-010-11 1,800.0

U 18 6801CoalSilo Ct 115563 - Coal Silo Bay

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 6801CoalSilo Transfer Conveyor Head Normal - Steady

State

E18 CD17 (P)

CD18 (P)

PT12 PT18 

3-05-010-11 3-05-102-05 

0.0 1,800.0 A 

OS2 6801CoalSilo Silo Feed System -

Conveyor & Tripper #1

Normal - SteadyState

E19 CD18 (P) PT18 3-05-010-11 1,800.0

OS3 6801CoalSilo Silo Feed System -

Conveyor & Tripper #2

Normal - SteadyState

E20 CD18 (P) PT18 3-05-010-11 1,800.0

OS4 6801CoalSilo Coal Silo (1) Normal - Steady

State

E21 CD18 (P) PT18 3-05-010-11 1,800.0

OS5 6801CoalSilo Coal Silo (2) Normal - Steady

State

E22 CD18 (P) PT18 3-05-010-11 1,800.0

Page 4 of 8
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 18 6801CoalSilo Ct 115563 - Coal Silo Bay

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS6 6801CoalSilo Coal Silo (3) Normal - Steady

State

E23 CD18 (P) PT18 3-05-010-11 1,800.0

OS7 6801CoalSilo Coal Silo (4) Normal - Steady

State

E24 CD18 (P) PT18 3-05-010-11 1,800.0

OS8 6801CoalSilo Coal Silo (5) Normal - Steady

State

E25 CD18 (P) PT18 3-05-010-11 1,800.0

OS9 6801CoalSilo Coal Silo (6) Normal - Steady

State

E26 CD18 (P) PT18 3-05-010-11 1,800.0

OS10 6801CoalSilo Coal Silo (7) Normal - Steady

State

E27 CD18 (P) PT18 3-05-010-11 1,800.0

OS11 6801CoalSilo Coal Silo (8) Normal - Steady

State

E28 CD18 (P) PT18 3-05-010-11 1,800.0

U 30 5201AshTrans Ct 115564 - Ash Transfer System

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 5201AshTrans Ash Transfer System Normal - Steady

State

E30 CD30 (P) PT30 

PT31 PT32 PT33 

3-05-010-99 3,560.0

Page 5 of 8
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 34 5101AshRecyc Ct 115558 - Ash Recycle Silo

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 5101AshRecyc Ash Recycle Silo Normal - Steady

State

E34 CD34 (P) PT34 3-05-102-99 8,760.0

U 35 Ash Mixer Ash Mixer normal operation (mix ash with water)

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 Ash Mixer Ash Mixer normal

operation (mix ash withwater)

Normal - SteadyState

E35 CD35 (P) PT35 0.0 1,000.0 

Page 6 of 8
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 36 5200AshStorS Ct 115559 - Ash Storage Silo and Unloader

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 5200AshStorS Ash Storage Silo and

Unloader

Normal - SteadyState

E36 CD36 (P) PT36 3-05-102-99 1,600.0

U 37 5102LimeSlur Ct 099322 - Lime Silo

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 5101LimeSlur Lime Silo Normal - Steady

State

E37 CD37 (P) PT37 3-05-102-05 0.0 2,000.0 A 

Page 7 of 8
New Jersey Department of Environmental Protection

Emission Unit/Batch Process Inventory

CARNEYS POINT GENERATING PLANT (65498)BOP120002

U 38 DetroitDiese Ct 117297 - Diesel Fire Pump

UOS

NJID

Facility's

Designation

UOS

Description

Operation

Type

Signif.

Equip.

Control

Device(s)

Emission

Point(s) SCC(s)

Annual

Oper. Hours

Min. Max.

VOC

 Range

OS1 DetroitDiese Detroit Diesel

DDFP-06FA-8175

Normal - SteadyState

E38 PT38 2-03-001-01 

Page 8 of 8
New Jersey Department of Environmental Protection

Subject Item Group Inventory

Group NJID: GR1 PCBoilSum

Members: Type ID OS Step 

U U 1 OS0 SummaryU U 2 OS0 Summary

Formal Reason(s) for Group/Cap:

9 Other

Other (explain): fuel and emission caps, consolidate duplicate requirements

Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group: Operating Circumstances:

Page 1 of 5
New Jersey Department of Environmental Protection

Subject Item Group Inventory

Group NJID: GR2 PCBoilOS1

Members: Type ID OS Step 

U U 1 OS1 CoaBoil1U U 2 OS1 CoaBoil2

Formal Reason(s) for Group/Cap:

9 Other

Other (explain): fuel and emission caps

Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group: Operating Circumstances:

Page 2 of 5
New Jersey Department of Environmental Protection

Subject Item Group Inventory

Group NJID: GR3 PCBoilS/U

Members: Type ID OS Step 

U U 1 OS2 S/U Boiler1U U 2 OS2 S/U Boiler2

Formal Reason(s) for Group/Cap:

9 Other

Other (explain): fuel and emission caps

Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group: Operating Circumstances:

Page 3 of 5
New Jersey Department of Environmental Protection

Subject Item Group Inventory

Group NJID: GR4 PCBoilS/D

Members: Type ID OS Step 

U U 1 OS3 S/D Boiler1U U 2 OS3 S/D Boiler2

Formal Reason(s) for Group/Cap:

9 Other

Other (explain): fuel and emission caps

Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group: Operating Circumstances:

Page 4 of 5
New Jersey Department of Environmental Protection

Subject Item Group Inventory

Group NJID: GR5 CoalPrepStds

Members: Type ID OS Step 

U U 10 OS0 SummaryU U 11 OS0 SummaryU U 13 OS0 SummaryU U 14 OS0 SummaryU U 18 OS0 Summary

Formal Reason(s) for Group/Cap:

9 Other

Other (explain): NSPS Subparts A & Y for Coal Preparation Plants

Condition/Requirements that will be complied with or are no longerapplicable as a result of this Group: Operating Circumstances:

Page 5 of 5
Attachement: CAIR PERMIT

 CHRIS CHRISTIE DEPARTMENT of ENVIRONMENTAL PROTECTION BOB MARTIN 

 Governor Commissioner

Division of Air Quality

 KIM GUADAGNO Bureau of Air Permits 

 Lt. Governor 401 E. State Street, 2nd floor, P.O. Box 27 

Trenton, NJ 08625-0027 
Clean Air Interstate Rule (CAIR) permit 

Issued to: Carneys Point Generating Station 

500 Shell Road 

Carneys Point NJ 08069 

Owned by: Chambers Cogeneration, LP500 Shell Road 

Carneys Point NJ 08069 

 

Operated by: Chambers Cogeneration, LP500 Shell Road 

Carneys Point NJ 08069 

ORIS Code: 10566 

Effective: April 5, 2010 through March 27 2013 

This CAIR permit is issued under the authority of Chapter 106, P.L. 1967 (N.J.S.A. 26:2C-9.2), 42 U.S.C. 7401, 

7403, 7410, 7426, 7601, and 7651, et seq., and Title V of the Clean Air Act. The owners and operators of each 

affected unit at this facility shall comply with all of the requirements established in this permit. 

Approved by: 

_________________________________ 

Aliya M. Khan 

Bureau of Air Permits 

 CHRIS CHRISTIE DEPARTMENT of ENVIRONMENTAL PROTECTION BOB MARTIN 

 Governor Commissioner

Division of Air Quality

 KIM GUADAGNO Bureau of Air Permits 

 Lt. Governor 401 E. State Street, 2nd floor, P.O. Box 27 

Trenton, NJ 08625-0027
CAIR PERMIT CONTENTS 

1) STATEMENT OF BASIS 

2) UNIT SPECIFIC REQUIREMENTS 

3) COMMENTS, NOTES, AND JUSTIFICATIONS REGARDING PERMIT DECISIONS 

4) CAIR PERMIT APPLICATION 
1) Statement of Basis 

In accordance with N.J.S.A. 26:2C-9.2, 42 U.S.C. 7401, 7403, 7410, 7426, 7601, and 7651, et seq., and 

Title V of the Clean Air Act, the Department issues this permit pursuant to N.J.A.C. 7:27 et seq. 

2) Unit Specific Requirements 

The number of allowances is allocated to CAIR affected units by USEPA.. 

3) Comments, Notes, And Justifications Regarding Permit Decisions 

None. 

4) CAIR Permit Application 

The owners and operators shall comply with all of the standard requirements and special provisions set 

forth on the attached CAIR Application for each affected unit.