Name: Kevin Holbrooks

Title: Director, Environmental Compliance

Company: St. Johns River Power Park

Sign Date:

Name: Carl Vineyard

Title: Utility MACT Program Director

Company: Grace Consulting, Inc.

Sign Date: 6/25/2010

Permitted Facility Representative / Date Testing Company Representative / Date

St. Johns River Power Park, Unit 2

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, February 04, 2011 Page 1 of 13
St. Johns River Power Park, Unit 2

Facility Information:

St. Johns River Power Park

11201 New Berlin Road

Jacksonville FL 32226

Contact: Kevin Holbrooks

Phone: 904-665-4540

Fax: 904-665-4530

Email: holbke@jea.com

Testing Company:

Grace Consulting, Inc.

510 Dickson Street

Wellington OH 44090

Contact:Carl Vineyard

Phone: 440-647-6672

Fax: 440-467-6673

Email: carlvineyard@aol.com

Air Permit Number:

FL0037869

Permitted Source ID/Name:

SJRPP Unit 2

Permitted Maximum Process Rate:

660 MW

Max. Normal Operation Process Rate:

660 MW

Target Process Test Rate

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

SJRPP Unit 2 is a pulverized coal boiler rated at 660MW with a SCR, Electrostatic Precipitator and Scrubber

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 1203100001 FRS #: 110000362134

SCC / Description 10100202 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Bituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Unit 2 471.44 0 0 0 2350 600 4 24

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Unit 2 Carbon Monoxide Method 10 3 120 0

Total organic compounds 

(TOC) as Propane

Stack Unit 2 Method 25A 3 120 0

Stack Unit 2 O2 Method 3A O2 3 120 0

Stack Unit 2 Co2 Method 3A CO2 3 120 0

Stack Unit 2 Nitrogen oxides (NOx) Method 7E 3 120 0

Friday, February 04, 2011 Page 2 of 13
St. Johns River Power Park, Unit 2

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

There were no modifications to the testing methods.

Friday, February 04, 2011 Page 3 of 13
St. Johns River Power Park, Unit 2

Sampling / Stack Data Results Summary

Location Stack Unit 2 - Method 10

Average

Run Number 1 2 3

Test Date 4/7/2010 4/7/2010 4/7/2010

Run Start Time 6:50:00 AM 9:25:00 

AM

11:55:00 AM

Run Finish Time 9:00:00 AM 11:33:00 

AM

2:05:00 PM

Carbon Dioxide, % 12.6 12.8 12.8 12.733

Oxygen, % 6.7 6.6 6.6 6.633

Dry Volumetric Flow Rate, dry scfm 1861147 1858073 1843269 1,854,163.00

0

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.51 12.25 14.2 13.320

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Location Stack Unit 2 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, February 04, 2011 Page 4 of 13
St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Unit 2 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, February 04, 2011 Page 5 of 13
St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, February 04, 2011 Page 6 of 13
St. Johns River Power Park, Unit 2

Emissions Summary

Process Run Data

Location: Stack Unit 2 - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 6.72E-02 7.97E-02 1.41E-01 0.096

ppm 6.42E+01 7.67E+01 1.36E+02 92.300

ppm@7%O2 6.28E+01 7.46E+01 1.32E+02 89.800

Location: Stack Unit 2 - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 7.91E-04 9.79E-04 1.51E-03 0.001

ppm 4.80E-01 5.98E-01 9.21E-01 0.666

ppm@7%O2 4.70E-01 5.81E-01 8.95E-01 0.649

Location: Stack Unit 2 - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 6.10E-02 7.97E-02 8.57E-02 0.075

ppm 3.55E+01 4.67E+01 5.02E+01 44.133

ppm@7%O2 3.48E+01 4.54E+01 4.88E+01 43.000

Friday, February 04, 2011 Page 7 of 13
St. Johns River Power Park, Unit 2

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 5970 mmBTU 5800

2 Heat Input 6019 mmBTU 5800

3 Heat Input 6025 mmBTU 5800

1 Steam Flow 4.67 Mlb/hr 4.5

2 Steam Flow 4.74 Mlb/hr 4.5

3 Steam Flow 4.74 Mlb/hr 4.5

1 Gross MW 543 MW 650

2 Gross MW 670 MW 650

3 Gross MW 630 MW 650

Run Name Value UOM Comments

Target

Value

1 SCR (SELECTIVE CATALYTIC REDUCTION) 814 lb/hr 775

2 SCR (SELECTIVE CATALYTIC REDUCTION) 819 lb/hr 775

3 SCR (SELECTIVE CATALYTIC REDUCTION) 796 lb/hr 775

1 DUAL ALKALI SCRUBBING 112 Kgpm 108

2 DUAL ALKALI SCRUBBING 113 Kgpm 108

3 DUAL ALKALI SCRUBBING 112 Kgpm 108

1 ELECTROSTATIC PRECIPITATOR

2 ELECTROSTATIC PRECIPITATOR

3 ELECTROSTATIC PRECIPITATOR

1 OVERFIRE AIR

2 OVERFIRE AIR

3 OVERFIRE AIR

Friday, February 04, 2011 Page 8 of 13
St. Johns River Power Park, Unit 2

Sampling / Stack Data Results Detail

Location Stack Unit 2 - Method 10

Average

Run Number 1 2 3

Test Date 4/7/2010 4/7/2010 4/7/2010

Run Start Time 6:50:00 AM 9:25:00 AM 11:55:00 AM

Run Finish Time 9:00:00 AM 11:33:00 AM 2:05:00 PM

Carbon Dioxide, % 12.6 12.8 12.8 12.733

Oxygen, % 6.7 6.6 6.6 6.633

Fuel Factor 1.13 1.12 1.12

Dry Volumetric Flow Rate, dry scfm 1861147 1858073 1843269 1,854,163.0

00

F-Factor, dscfm/MMBtu @ %O2 9780 9780 9780 9,780.000

Moisture, % 13.51 12.25 14.2 13.320

Analyzer Make Horiba Horiba Horiba

Analyzer Model VIA-510 VIA-510 VIA-510

Analyzer Serial Number 570124044 570124044 570124044 570,124,044

.000

Operating Range 497 497 497 497.000

Operating Units ppm ppm ppm

No. Readings/Avg. 120 120 120 120.000

Calibration Set 1 1 1 1.000

Calibration Pre Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Pre Zero Cylinder Instrument Response 1.15 0.03 2.98 1.387

Calibration Pre Zero Cylinder Bias 0.22 0 0.59 0.270

Calibration Pre Zero Cylinder Drift 0 0 0 0.000

Calibration Pre High Cylinder ID EB0004477 EB0004477 EB0004477

Calibration Pre High Cylinder Instrument Response 233.39 231.12 230.17 231.560

Calibration Pre High Cylinder Bias 0.22 -0.24 -0.43 -0.150

Calibration Pre High Cylinder Drift 0 0 0 0.000

Calibration Post Zero Cylinder ID EB0020770 EB0020770 EB0020770

Calibration Post Zero Cylinder Instrument Response 0.03 2.98 2.28 1.763

Calibration Post Zero Cylinder Bias 0 0.59 0.45 0.347

Calibration Post Zero Cylinder Drift 0.22 0.59 0.14 0.317

Calibration Post High Cylinder ID EB0004477 EB0004477 EB0004477

Calibration Post High Cylinder Instrument Response 231.12 230.17 235.72 232.337

Calibration Post High Cylinder Bias -0.24 -0.43 0.69 0.007

Calibration Post High Cylinder Drift 0.46 0.19 1.12 0.590

Cavg 65.3 77.9 138.93 94.043

Cavg Units ppmvd ppmvd ppmvd

Cgas 64.2449 76.6817 136.1136 92.347

Cgas Units ppmvd ppmvd ppmvd

Fuel Type Coal - 

Bituminous

Coal - 

Bituminous

Coal - 

Bituminous

Fw 10640 10640 10640 10,640.000

Fc 1800 1800 1800 1,800.000

Cgasw 0 0 0 0.000

Cgasw Units

Friday, February 04, 2011 Page 9 of 13
St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 04, 2011 Page 10 of 13
St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 04, 2011 Page 11 of 13
St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 04, 2011 Page 12 of 13
St. Johns River Power Park, Unit 2

Location Stack Unit 2 - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 04, 2011 Page 13 of 13