EMISSIONS TEST REPORT 

POLK POWER STATION 

FACILITY ID NUMBER: 1050233 

EMISSION UNIT ID NO: -001 

UNIT 1 

SYNTHETIC GAS 

CARBON MONOXIDE, VISIBLE EMISSIONS EVALUATION, and 

OXIDES OF NITROGEN, SULFUR DIOXIDE FROM CEMS 

January 8, 2008 

Prepared For: 

Tampa Electric Company 

Polk Power Station 

P.O. Box 111 

Tampa, Florida 33601-0111 

Prepared By: 

Tampa Electric Company 

Environmental, Health, & Safety 

Air Services Group 

Environmental, Health, & Safety 

Air Services Group 

5010 Causeway Boulevard 

Tampa, Florida 33619- 6130 
REPORT CERTIFICATION 

 The sampling and subsequent data entry/reduction detailed in this report 

was conducted at my direction, and I hereby certify that this test report is 

authentic and accurate to the best of my knowledge. 

Signature:__________________________ 

Jorge A. Varino 

Environmental Technician 

Test Team Lead 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the test performance, associated quality assurance 

activities, the resultant calculations, and the contents of this report, and certify 

that all project quality objectives have been met. This report is approved for 

submittal. 

Signature:__________________________ 

Raymond A. McDarby, Jr. 

Senior Environmental Technician 

Quality Assurance/Quality Control Specialist 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

 I have reviewed the testing details and results submitted in this report, 

and hereby certify that this test report is authentic and accurate to the best of 

my knowledge. 

Signature:__________________________ 

David A. Smith 

Coordinator – Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 
TABLE OF CONTENTS

SECTION PAGE NO.

1.0 INTRODUCTION 1 

2.0 DISCUSSION OF RESULTS 2 

 EXECUTIVE SUMMARY 2 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES 4 

4.0 TABULATED RESULTS 

CARBON MONOXIDE TEST DATA 6 

NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 7 

HEAT INPUT CALCULATIONS 8 

5.0 STACK SAMPLING LOCATION DIAGRAM 10 

APPENDICES

A. CARBON MONOXIDE TEST INFORMATION

SUMMARIZED RUN DATA & QA/QC 

TEST RUN LOG 

CYLINDER GAS CERTIFICATES 

B. TURBINE DATA

C. FUEL ANALYSIS

D. CEMS DATA

E. VISIBLE EMISSION DATA SHEET

F. TEST PARTICIPANTS
1 

1.0 INTRODUCTION

On January 8, 2008, Tampa Electric Company’s, Environmental Services, Air Services 

Group performed Carbon Monoxide (CO), Volatile Organic Compounds (VOC) source 

emission tests, and Visible Emissions Observations on Unit No. 1 at the Polk Power 

Station. Unit No. 1 is a combined cycle combustion turbine generating unit. The 

combustion turbine was fired with syngas from the solid fuel gasification system. A 

blend of petroleum coke and bituminous coal was gasified for this test. Testing was 

conducted according to United States Environmental Protection Agency (USEPA) test 

methods stipulated in 40 CFR Part 60, Appendix A and Florida Department of 

Environmental Protection (FDEP) Permit No. 1050233-016-AV. Testing was conducted 

concurrent with the annual 40CFR75 Relative Accuracy Test Audit (RATA) for this unit. 

Nitrogen Oxides (NOx) and Sulfur Dioxide (SO2) data was taken from the Continuous 

Emissions Monitoring System’s (CEMS) Data Acquisition and Handling System (DAHS) 

and is presented as averages over the test period. 
2 

2.0 DISCUSSION OF RESULTS

Executive Summary 

Tampa Electric Company 

Polk Power Station 

General Electric 7F Combined Cycle Combustion Turbine 

Emission Unit ID -001 

Solid Fuel Derived Synthetic Gas 

Compliance Parameter Test Result FDEP Permit Limit 

CO, ppmvd @15% O2 4 25 

CO, lbs/hr 16 98 

VE, % opacity 0 10 

NOX, lbs/hr 101.87 220.25 

SO2, lbs/hr 321 357 

Heat Input, mmBtu/hr 1717 -- 

Maximum Heat Input 1 1751 -- 

Unit Load (% of permit) 2 98% 90 – 100% 

1Maximum Heat Input is Permitted Maximum Heat Input Rate, 1755 mmBtu/hr @ 59o F, 

Corrected to Average Ambient Temperature Recorded During the Test Period. 

2Unit Load (% of permit) is Heat Input Divided by Maximum Heat Input times 100. 

The Carbon Monoxide (CO) concentration and emission rate was derived from three 1-

hour test runs. The calculated average CO concentration was 4 ppmvd @ 15% O2. 

The calculated average emission rate was 16 lbs/hr. The FDEP permitted 

concentration is 25 ppmvd @15% O2. The FDEP permitted emission rate is 98 lbs/hr 

based on a 30-day rolling average. 

The Visible Emissions Observations (VEO) yielded an average opacity of 0% for the 1-

hour test. The FDEP permitted opacity is 10 percent. 

During the CO testing, the Nitrogen Oxides (NOx) average emission rate was 101.87 

lbs/hr. 

During the CO testing, the Sulfur Dioxide (SO2) average emission rate was 321 lbs/hr. 
3 

During the test Unit No. 1 was operated at an average heat input of 1717 mmBtu/hr. 

The FDEP permitted heat input is 1755 mmBtu/hr, at an ambient temperature of 59o 

(corrected to 1751 mmBtu/hr based on an average inlet vane temperature of 77o F, and 

the manufacturer’s heat input correction curve for this unit). The unit operated at 98% 

of permitted capacity. 
4 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generating Station is located at County Road 630 approximately 

13 miles southwest of Bartow, Polk County, Florida. Unit No. 1 is a Combined Cycle 

Combustion Turbine generating unit, with a net capacity of 192 MW when fired with 

Syngas fuel. The source sampling location consists of a circular stack 19 feet in 

diameter with four sample ports located 90 degrees apart on the stack circumference. 

A diagram of the stack sampling location is included along with other pertinent 

information on the test site. 

Carbon Monoxide sampling was performed in accordance with USEPA Reference 

Method 10 (40 CFR Part 60, Appendix A) “Determination of Carbon Monoxide 

Emissions From Stationary Sources”. Testing was performed using a Thermo 

Environmental Instruments model 48C Carbon Monoxide Analyzer. Testing was 

conducted concurrently with the annual USEPA 40CFR75 Relative Accuracy Test Audit 

(RATA) for this unit. 

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. 

This data was taken as 1-minute averages over the time frame from 10:46 on January 

8, 2008 through 17:00 on January 8, 2008, representing the time frame of the CO test. 

Plant operational data was taken from the Plant Information (PI) server system. Data 

captured included the minute average load, minute fuel flow, minute inlet vane 

temperature, and minute saturator readings from 10:46 on January 8, 2008 through 

17:00 on January 8, 2008. 
5 

4.0 TABULATED RESULTS
POLK POWER STATION

CARBON MONOXIDE DATA

CO % O2 CO, ppmvd CO

Run # Start Stop ppmvd volume @ 15% O2 lbs/hr

1 10:46 12:20 6.48 11.51 4.07 15.37

2 12:39 13:00 6.40 11.54 4.03 15.23

3 13:14 13:35 6.24 11.58 3.95 14.91

4 13:48 14:09 6.37 11.52 4.01 15.13

5 14:19 14:40 6.31 11.57 3.99 15.06

6 14:55 15:16 6.67 11.53 4.20 15.86

7 15:32 15:53 6.79 11.53 4.28 16.14

8 16:07 16:28 7.00 11.46 4.38 16.52

9 16:39 17:00 6.87 11.50 4.31 16.28

Averages: 4.135 15.610

CO, ppmvd @ 15% O2 is calculated as:

CO, ppmvd x (5.9 / (20.9 - % O2, volume))

CO, lbs/hr is calculated as:

CO, ppmvd x Cf x Fd x (20.9 / (20.9 - % O2, volume) x Heat Input

where: Cf = 7.27249E-08 lb/scf

Fd = 8534 dscf/mmBtu

Heat Input = 1717 mmBtu/hr

Test Times

RM Data Calculated Data

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

January 8, 2008

6 
POLK POWER STATION

NO X & SO 2 COMPLIANCE DATA FROM CEMS

NOx SO2 Flow NOx SO2

ppmvw ppmvw kscfmw lbs/hr lbs/hr

16.97 38.49 837.87 101.87 321

NOX, lbs/hr calculated as:

NOX, ppmvw x 1.194E-07 x Flow, kscfmw x 60 min/hr x 1000/k

SO2, lbs/hr calculated as:

SO2, ppmvw x 1.660E-07 x Flow, kscfmw x 60 min/hr x 1000/k

CEM Data Calculated Data

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

January 8, 2008

7 
POLK POWER STATION

HEAT INPUT CALCULATION

Average fuel flow: 7124.8504 Kcfh

Mole weight correction to meter cal: 0.9883 mole weight correction factor

Corrected fuel flow:1 7041.4897 Kcfh, corrected for density

Average moisture: 1.31 % H20 added to fuel

Corrected fuel flow:2 6949.1249 Kscfh, corrected for moisture

Gross heating value of fuel (HHV): 247.10 Btu/scf

Heat Input: 1717 mmBtu/hr

Average fuel flow from Plant Information Data Base.

Mole weight correction factor to meter calibration is taken from ratio of syngas mole weight

to calibration gas mole weight.

1Average fuel flow times mole weight correction factor.

2Corrected fuel flow times (1 - (Average moisture / 100)).

Gross Heating value of fuel (HHV) is from fuel analysis.

Heat input is (HHV x Corrected fuel flow) / 1000.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

January 8, 2008

8 
9 

5.0 SAMPLING LOCATION DIAGRAM
10 

UNFIRED HEAT 

RECOVERY 

BOILER 

TRANSITION 

DUCT 

EXHAUST FROM 

TURBINE 

14 FT. 

38 FT. 

150 FT. 

136 FT. 

POLK POWER STATION

COMBUSTION TURBINE

COMBINED CYCLE UNIT NO.1 

TEST LOCATION 

PORT LOCATION PLAN

19.0 FT.ID. 

STACK DIAMETERS DOWNSTREAM

FROM DISTURBANCE = 2.0 

STACK DIAMETERS UPSTREAM

FROM DISTURBANCE = 0.7 

STACK DIAMETER = 19.0 FT. 

STACK AREA = 283.529 SQ. FT.

STACK AREA =40828.138 SQ. IN. 
APPENDIX A 

CARBON MONOXIDE TEST INFORMATION 
SUMMARIZED RUN DATA & QA/QC 
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 1

01/08/2008 10:46:01 12:20:09

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.047 0.044 0.001

Span 10.574 9.378 7.986

Final Readings

Zero 0.07 0.085 0.032

Span 10.556 9.406 8.016

System Bias (Eq 7E-2)

Initial Zero Bias SB -0.01 0.09 0.24

Initial Span Bias SB -0.01 1.3 -0.39

Final Zero Bias SB 0.1 0.32 0.62

Final Span Bias SB -0.1 1.46 -0.01

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.22 0.24 0.01

Initial Span SCE 0.35 2.1 -0.67

Final Zero SCE 0.33 0.47 0.4

Final Span SCE 0.27 2.26 -0.3

Drift Assessment (Eq 7E-4)

Zero Drift D 0.11 0.23 0.38

Span Drift D 0.09 0.16 0.38

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.58 9.69 6.45

Corrected Results (ppmv) 11.51 9.29 6.48

Page 1 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 2

01/08/2008 12:39:43 13:00:44

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.07 0.085 0.032

Span 10.556 9.406 8.016

Final Readings

Zero 0.075 0.058 -0.03

Span 10.549 9.341 7.916

System Bias (Eq 7E-2)

Initial Zero Bias SB 0.1 0.32 0.62

Initial Span Bias SB -0.1 1.46 -0.01

Final Zero Bias SB 0.12 0.17 -0.12

Final Span Bias SB -0.13 1.09 -1.26

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.33 0.47 0.4

Initial Span SCE 0.27 2.26 -0.3

Final Zero SCE 0.36 0.32 -0.35

Final Span SCE 0.23 1.89 -1.54

Drift Assessment (Eq 7E-4)

Zero Drift D 0.02 0.15 0.74

Span Drift D 0.03 0.37 1.25

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.59 9.68 6.34

Corrected Results (ppmv) 11.54 9.3 6.4

Page 2 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 3

01/08/2008 13:14:28 13:35:28

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.075 0.058 -0.03

Span 10.549 9.341 7.916

Final Readings

Zero 0.07 0.081 -0.03

Span 10.508 9.333 7.917

System Bias (Eq 7E-2)

Initial Zero Bias SB 0.12 0.17 -0.12

Initial Span Bias SB -0.13 1.09 -1.26

Final Zero Bias SB 0.1 0.29 -0.12

Final Span Bias SB -0.33 1.05 -1.24

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.36 0.32 -0.35

Initial Span SCE 0.23 1.89 -1.54

Final Zero SCE 0.33 0.45 -0.35

Final Span SCE 0.04 1.85 -1.53

Drift Assessment (Eq 7E-4)

Zero Drift D 0.02 0.12 0

Span Drift D 0.2 0.04 0.02

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.6 9.65 6.14

Corrected Results (ppmv) 11.58 9.3 6.24

Page 3 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 4

01/08/2008 13:48:37 14:09:38

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.07 0.081 -0.03

Span 10.508 9.333 7.917

Final Readings

Zero 0.047 0.044 0.001

Span 10.574 9.378 7.986

System Bias (Eq 7E-2)

Initial Zero Bias SB 0.1 0.29 -0.12

Initial Span Bias SB -0.33 1.05 -1.24

Final Zero Bias SB -0.01 0.09 0.24

Final Span Bias SB -0.01 1.3 -0.39

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.33 0.45 -0.35

Initial Span SCE 0.04 1.85 -1.53

Final Zero SCE 0.22 0.24 0.01

Final Span SCE 0.35 2.1 -0.67

Drift Assessment (Eq 7E-4)

Zero Drift D 0.11 0.2 0.36

Span Drift D 0.32 0.25 0.85

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.56 9.64 6.3

Corrected Results (ppmv) 11.52 9.28 6.37

Page 4 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 5

01/08/2008 14:19:50 14:40:51

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.052 0.048 -0.03

Span 10.495 9.276 7.906

Final Readings

Zero 0.034 0.013 -0.16

Span 10.5 9.219 7.917

System Bias (Eq 7E-2)

Initial Zero Bias SB 0.01 0.11 -0.12

Initial Span Bias SB -0.39 0.73 -1.38

Final Zero Bias SB -0.08 -0.08 -1.75

Final Span Bias SB -0.37 0.42 -1.24

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.25 0.27 -0.35

Initial Span SCE -0.02 1.53 -1.67

Final Zero SCE 0.16 0.07 -1.98

Final Span SCE 0 1.22 -1.53

Drift Assessment (Eq 7E-4)

Zero Drift D 0.09 0.19 1.63

Span Drift D 0.02 0.31 0.14

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.56 9.64 6.19

Corrected Results (ppmv) 11.57 9.38 6.31

Page 5 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 6

01/08/2008 14:55:35 15:16:35

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.034 0.013 -0.16

Span 10.5 9.219 7.917

Final Readings

Zero 0.032 0.05 0.011

Span 10.488 9.201 7.956

System Bias (Eq 7E-2)

Initial Zero Bias SB -0.08 -0.08 -1.75

Initial Span Bias SB -0.37 0.42 -1.24

Final Zero Bias SB -0.09 0.12 0.36

Final Span Bias SB -0.43 0.32 -0.76

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.16 0.07 -1.98

Initial Span SCE 0 1.22 -1.53

Final Zero SCE 0.15 0.28 0.14

Final Span SCE -0.06 1.12 -1.04

Drift Assessment (Eq 7E-4)

Zero Drift D 0.01 0.2 2.11

Span Drift D 0.06 0.1 0.48

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.52 9.54 6.57

Corrected Results (ppmv) 11.53 9.32 6.67

Page 6 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 7

01/08/2008 15:32:57 15:53:57

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.032 0.05 0.011

Span 10.488 9.201 7.956

Final Readings

Zero 0.029 -0.009 -0.13

Span 10.483 9.176 7.946

System Bias (Eq 7E-2)

Initial Zero Bias SB -0.09 0.12 0.36

Initial Span Bias SB -0.43 0.32 -0.76

Final Zero Bias SB -0.1 -0.21 -1.38

Final Span Bias SB -0.45 0.18 -0.88

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.15 0.28 0.14

Initial Span SCE -0.06 1.12 -1.04

Final Zero SCE 0.14 -0.05 -1.6

Final Span SCE -0.08 0.98 -1.17

Drift Assessment (Eq 7E-4)

Zero Drift D 0.01 0.33 1.74

Span Drift D 0.02 0.14 0.12

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.51 9.54 6.71

Corrected Results (ppmv) 11.53 9.35 6.79

Page 7 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 8

01/08/2008 16:07:43 16:28:44

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.029 -0.009 -0.13

Span 10.483 9.176 7.946

Final Readings

Zero 0.047 0.044 0.001

Span 10.574 9.378 7.986

System Bias (Eq 7E-2)

Initial Zero Bias SB -0.1 -0.21 -1.38

Initial Span Bias SB -0.45 0.18 -0.88

Final Zero Bias SB -0.01 0.09 0.24

Final Span Bias SB -0.01 1.3 -0.39

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.14 -0.05 -1.6

Initial Span SCE -0.08 0.98 -1.17

Final Zero SCE 0.22 0.24 0.01

Final Span SCE 0.35 2.1 -0.67

Drift Assessment (Eq 7E-4)

Zero Drift D 0.09 0.3 1.62

Span Drift D 0.44 1.12 0.49

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.49 9.51 6.93

Corrected Results (ppmv) 11.46 9.23 7

Page 8 of 9
LabView QA Report

Polk Unit 1 CO Compliance - Report

RUN 9

01/08/2008 16:39:22 17:00:23

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO

Analyzer Range 250 200 10

Units % PPM PPM

Low Level Certified Value (PPM or %)

Mid Level Certified Value (PPM or %) 10.5 9 3.94

High Level Certified Value (PPM or %) 20.9 18 8.04

Zero Level Observed 0.05 0.028 -0.02

Low Level Observed - - -

Mid Level Observed 10.577 9.144 4.074

High Level Observed 20.971 17.983 8.017

Zero Calibration Error ACE 0.24 0.16 -0.22

Low Level Calibration Error ACE 0 0 0

Mid Level Calibration Error ACE 0.37 0.8 1.67

High Level Calibration Error ACE 0.34 -0.09 -0.29

Initial Readings

Zero 0.029 0.05 -0.11

Span 10.455 9.16 7.976

Final Readings

Zero 0.047 0.044 0.001

Span 10.574 9.378 7.986

System Bias (Eq 7E-2)

Initial Zero Bias SB -0.1 0.12 -1.13

Initial Span Bias SB -0.58 0.09 -0.51

Final Zero Bias SB -0.01 0.09 0.24

Final Span Bias SB -0.01 1.3 -0.39

System Calibration Error (Eq 7E-3)

Initial Zero SCE 0.14 0.28 -1.36

Initial Span SCE -0.22 0.89 -0.8

Final Zero SCE 0.22 0.24 0.01

Final Span SCE 0.35 2.1 -0.67

Drift Assessment (Eq 7E-4)

Zero Drift D 0.09 0.03 1.37

Span Drift D 0.57 1.21 0.12

Effluent Gas Concentration (Eq 7E-5)

Raw Results 11.51 9.49 6.81

Corrected Results (ppmv) 11.5 9.22 6.87

Page 9 of 9
TEST RUN LOG 
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 7:13:59 AM 21.09 -0.04 0.17

01/08/2008 7:14:29 AM 21.08 -0.04 0.14

01/08/2008 7:14:59 AM 21.08 -0.04 0.15

01/08/2008 7:15:29 AM 21.07 -0.03 0.1

01/08/2008 7:15:59 AM 21.1 -0.04 -0.18

01/08/2008 7:16:29 AM 21.11 -0.05 -0.06

01/08/2008 7:16:59 AM 21.1 -0.03 0.03

01/08/2008 7:17:29 AM 21.09 -0.04 0.05

01/08/2008 7:17:59 AM 21.1 -0.03 0.01

01/08/2008 7:18:29 AM 21.1 -0.03 0.02

01/08/2008 7:18:59 AM 21.09 -0.04 0.01

01/08/2008 7:19:29 AM 21.08 -0.02 0

01/08/2008 7:19:59 AM 21.05 -0.02 0.01

01/08/2008 7:20:29 AM 21.06 -0.01 0

01/08/2008 7:20:59 AM 21.07 -0.02 0.01

01/08/2008 7:21:29 AM 21.07 -0.02 -0.01

01/08/2008 7:21:59 AM 21.06 -0.01 0.03

01/08/2008 7:22:29 AM 21.06 -0.01 -0.02

01/08/2008 7:22:59 AM 21.06 -0.01 -0.01

01/08/2008 7:23:29 AM 21.06 -0.01 -0.01

01/08/2008 7:23:59 AM 21.07 -0.01 -0.02

01/08/2008 7:24:29 AM 21.07 -0.01 0

01/08/2008 7:24:59 AM 21.06 0 -0.01

01/08/2008 7:25:29 AM 21.05 0 0.01

01/08/2008 7:25:59 AM 21.06 -0.01 -0.01

01/08/2008 7:26:29 AM 21.05 0 -0.01

01/08/2008 7:26:59 AM 21.05 0 -0.01

01/08/2008 7:27:29 AM 21.05 0 0.02

01/08/2008 7:27:59 AM 21.07 -0.01 -0.05

01/08/2008 7:28:29 AM 21.09 -0.04 -0.2

01/08/2008 7:28:59 AM 21.1 -0.05 -0.21

01/08/2008 7:29:29 AM 21.1 -0.05 -0.24

01/08/2008 7:29:59 AM 21.09 -0.04 -0.11

01/08/2008 7:30:29 AM 21.08 -0.02 -0.1

01/08/2008 7:30:59 AM 21.07 -0.02 -0.11

01/08/2008 7:31:29 AM 21.08 -0.03 -0.12

01/08/2008 7:31:59 AM 21.06 -0.02 -0.15

01/08/2008 7:32:29 AM 21.07 -0.03 -0.13

01/08/2008 7:32:59 AM 21.07 -0.02 -0.16

01/08/2008 7:33:29 AM 21.06 -0.02 -0.14

Page 1 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 7:33:59 AM 21.06 -0.02 -0.19

01/08/2008 7:34:29 AM 21.07 -0.02 -0.16

01/08/2008 7:34:59 AM 21.06 -0.01 -0.18

01/08/2008 7:35:29 AM 21.06 -0.01 -0.19

01/08/2008 7:35:59 AM 21.06 -0.02 -0.19

01/08/2008 7:36:29 AM 21.07 -0.02 -0.2

01/08/2008 7:36:59 AM 21.06 -0.01 -0.19

01/08/2008 7:37:29 AM 21.06 -0.01 -0.21

01/08/2008 7:37:59 AM 21.06 -0.01 -0.24

01/08/2008 7:38:29 AM 12.19 5.32 -0.24

01/08/2008 7:38:59 AM 10.64 8.82 -0.24

01/08/2008 7:39:29 AM 10.65 8.91 -0.24

01/08/2008 7:39:59 AM 10.65 8.93 -0.24

01/08/2008 7:40:29 AM Linearity Check 10.64 8.95 -0.24

01/08/2008 7:40:59 AM Linearity Check 10.65 8.96 -0.02

01/08/2008 7:41:29 AM Linearity Check 10.66 8.97 -0.01

01/08/2008 7:41:59 AM Linearity Check 10.74 8.97 0.15

01/08/2008 7:42:29 AM Linearity Check 20.88 0.53 0.49

01/08/2008 7:42:59 AM Linearity Check 21.1 -0.04 0.42

01/08/2008 7:43:29 AM Linearity Check 20.01 5.99 -0.17

01/08/2008 7:43:59 AM Linearity Check 19.98 12.46 -0.24

01/08/2008 7:44:29 AM Linearity Check 21.06 17.12 -0.24

01/08/2008 7:44:59 AM Linearity Check 21.12 17.6 -0.24

01/08/2008 7:45:29 AM Linearity Check 21.14 17.65 -0.24

01/08/2008 7:45:59 AM Linearity Check 21.15 17.69 -0.24

01/08/2008 7:46:29 AM Linearity Check 21.16 17.99 -0.24

01/08/2008 7:46:59 AM Linearity Check 21.01 18.01 -0.24

01/08/2008 7:47:29 AM Linearity Check 20.97 18.01 -0.24

01/08/2008 7:47:59 AM Linearity Check 18.94 17.34 -0.2

01/08/2008 7:48:29 AM Linearity Check 10.66 9.33 -0.05

01/08/2008 7:48:59 AM Linearity Check 10.57 9.15 -0.04

01/08/2008 7:49:29 AM Linearity Check 10.58 9.14 -0.04

01/08/2008 7:49:59 AM Linearity Check 10.38 9.13 3.21

01/08/2008 7:50:29 AM Linearity Check 0.56 0.62 7.9

01/08/2008 7:50:59 AM Linearity Check 0.07 -0.05 8.01

01/08/2008 7:51:29 AM Linearity Check 0.05 -0.07 8.03

01/08/2008 7:51:59 AM Linearity Check 0.05 -0.03 8

01/08/2008 7:52:29 AM Linearity Check 0.05 0.04 8.02

01/08/2008 7:52:59 AM Linearity Check 0.04 0.02 7.34

01/08/2008 7:53:29 AM Linearity Check 0.25 0.01 4.28

Page 2 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 7:53:59 AM Linearity Check 0.05 0.01 4.11

01/08/2008 7:54:29 AM Linearity Check 0.04 0.02 4.12

01/08/2008 7:54:59 AM Linearity Check 0.03 0.02 4.07

01/08/2008 7:55:29 AM Linearity Check 0.05 0.02 4.45

01/08/2008 7:55:59 AM Linearity Check 0.05 0.01 7.71

01/08/2008 7:56:29 AM Linearity Check 0.04 0.01 7.92

01/08/2008 7:56:59 AM Linearity Check 0.04 0.01 7.93

01/08/2008 7:57:29 AM Linearity Check 0.05 0.01 8.03

01/08/2008 7:57:59 AM Linearity Check 0.03 0.01 7.33

01/08/2008 7:58:29 AM Linearity Check 0.94 1.53 0.57

01/08/2008 7:58:59 AM Linearity Check 0.08 2.81 -0.12

01/08/2008 7:59:29 AM Linearity Check 0.02 3.66 -0.14

01/08/2008 7:59:59 AM Linearity Check 0.02 3.71 -0.15

01/08/2008 8:00:29 AM Linearity Check 0.02 3.73 -0.14

01/08/2008 8:00:59 AM Linearity Check 0.01 3.74 -0.16

01/08/2008 8:01:29 AM Linearity Check 0.01 3.74 -0.16

01/08/2008 8:01:59 AM Linearity Check 0.02 3.73 -0.16

01/08/2008 8:02:29 AM Linearity Check 0.02 3.74 -0.16

01/08/2008 8:02:59 AM Linearity Check 0.02 3.74 -0.16

01/08/2008 8:03:29 AM Linearity Check 0.01 3.74 -0.17

01/08/2008 8:03:59 AM Linearity Check 0.02 3.75 -0.17

01/08/2008 8:04:29 AM Linearity Check 0 3.75 -0.14

01/08/2008 8:04:59 AM Linearity Check 0.02 3.74 -0.16

01/08/2008 8:05:29 AM Linearity Check 0.02 3.75 -0.14

01/08/2008 8:05:59 AM Linearity Check 0.01 3.76 -0.18

01/08/2008 8:06:29 AM Linearity Check 0.02 3.75 -0.15

01/08/2008 8:06:59 AM Linearity Check 0.02 3.76 -0.17

01/08/2008 8:07:29 AM Linearity Check 0.02 3.75 -0.16

01/08/2008 8:07:59 AM Linearity Check 0.02 3.75 -0.17

01/08/2008 8:08:29 AM Linearity Check 0.02 3.75 -0.05

01/08/2008 8:08:59 AM Linearity Check 0.4 6.67 -0.03

01/08/2008 8:09:29 AM Linearity Check 0.01 8.06 -0.07

01/08/2008 8:09:59 AM Linearity Check 0 8.16 -0.06

01/08/2008 8:10:29 AM Linearity Check 0 8.16 -0.07

01/08/2008 8:10:59 AM Linearity Check 0 8.16 -0.08

01/08/2008 8:11:29 AM Linearity Check 0 8.17 -0.05

01/08/2008 8:11:59 AM Linearity Check 0 8.17 -0.08

01/08/2008 8:12:29 AM Linearity Check 0.01 8.16 -0.06

01/08/2008 8:12:59 AM Linearity Check 0.01 8.16 -0.08

01/08/2008 8:13:29 AM Linearity Check 9.66 6.29 0.53

Page 3 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 8:13:59 AM Linearity Check 20.94 0.13 0.41

01/08/2008 8:14:29 AM Linearity Check 20.99 0.08 0.43

01/08/2008 8:14:59 AM Linearity Check 20.94 0.11 0.57

01/08/2008 8:15:29 AM Linearity Check 20.89 0.11 0.5

01/08/2008 8:15:59 AM Linearity Check 20.84 0.1 0.58

01/08/2008 8:16:29 AM Linearity Check 20.8 0.11 0.45

01/08/2008 8:16:59 AM converter check - 1 20.77 0.1 0.46

01/08/2008 8:17:29 AM converter check - 1 20.76 0.1 0.4

01/08/2008 8:17:59 AM converter check - 1 20.73 0.09 0.43

01/08/2008 8:18:29 AM converter check - 1 20.73 0.1 0.42

01/08/2008 8:18:59 AM converter check - 1 20.73 0.09 0.42

01/08/2008 8:19:29 AM converter check - 1 20.71 0.1 0.49

01/08/2008 8:19:59 AM converter check - 1 20.72 0.09 0.7

01/08/2008 8:20:29 AM converter check - 1 20.72 0.09 0.68

01/08/2008 8:20:59 AM converter check - 1 20.72 0.1 0.66

01/08/2008 8:21:29 AM converter check - 1 20.71 0.09 0.62

01/08/2008 8:21:59 AM converter check - 1 20.71 0.09 0.5

01/08/2008 8:22:29 AM converter check - 1 20.71 0.09 0.52

01/08/2008 8:22:59 AM converter check - 1 20.72 0.09 0.55

01/08/2008 8:23:29 AM converter check - 1 20.72 0.09 0.46

01/08/2008 8:23:59 AM converter check - 1 20.72 0.08 0.52

01/08/2008 8:24:29 AM converter check - 1 20.71 0.08 0.57

01/08/2008 8:24:59 AM converter check - 1 20.71 0.08 0.67

01/08/2008 8:25:29 AM converter check - 1 20.71 0.07 0.55

01/08/2008 8:25:59 AM converter check - 1 20.68 0.07 0.54

01/08/2008 8:26:29 AM converter check - 1 20.69 0.07 0.6

01/08/2008 8:26:59 AM converter check - 1 20.68 0.08 0.51

01/08/2008 8:27:29 AM converter check - 1 20.67 0.08 0.49

01/08/2008 8:27:59 AM converter check - 1 20.68 0.07 0.49

01/08/2008 8:28:29 AM converter check - 1 20.66 0.08 0.52

01/08/2008 8:28:59 AM converter check - 1 20.66 0.09 0.48

01/08/2008 8:29:29 AM converter check - 1 20.66 0.08 0.44

01/08/2008 8:29:59 AM converter check - 1 20.67 0.08 0.45

01/08/2008 8:30:29 AM converter check - 1 20.66 0.09 0.51

01/08/2008 8:30:59 AM converter check - 1 20.67 0.09 0.5

01/08/2008 8:31:29 AM converter check - 1 20.67 0.08 0.49

01/08/2008 8:31:59 AM converter check - 1 20.68 0.08 0.5

01/08/2008 8:32:29 AM converter check - 1 20.67 0.07 0.42

01/08/2008 8:32:59 AM converter check - 1 20.68 0.08 0.51

01/08/2008 8:33:29 AM converter check - 1 20.68 0.08 0.43

Page 4 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 8:33:59 AM converter check - 1 20.67 0.08 0.46

01/08/2008 8:34:29 AM converter check - 1 20.69 0.07 0.57

01/08/2008 8:34:59 AM converter check - 1 20.7 0.08 0.67

01/08/2008 8:35:29 AM converter check - 1 20.71 0.07 0.72

01/08/2008 8:35:59 AM converter check - 1 20.71 0.07 0.77

01/08/2008 8:36:29 AM converter check - 1 20.72 0.07 0.6

01/08/2008 8:36:59 AM converter check - 1 20.72 0.06 0.52

01/08/2008 8:37:29 AM converter check - 1 20.71 0.06 0.53

01/08/2008 8:37:59 AM converter check - 1 20.72 0.06 0.51

01/08/2008 8:38:29 AM converter check - 1 20.71 0.07 0.55

01/08/2008 8:38:59 AM converter check - 1 20.71 0.07 0.54

01/08/2008 8:39:29 AM converter check - 1 20.72 0.07 0.51

01/08/2008 8:39:59 AM converter check - 1 20.71 0.07 0.56

01/08/2008 8:40:29 AM converter check - 1 20.7 0.06 0.71

01/08/2008 8:40:59 AM converter check - 1 20.71 0.05 0.74

01/08/2008 8:41:29 AM converter check - 1 20.7 0.06 0.72

01/08/2008 8:41:59 AM converter check - 1 20.7 0.06 0.67

01/08/2008 8:42:29 AM converter check - 1 20.7 0.06 0.54

01/08/2008 8:42:59 AM converter check - 1 20.68 0.06 0.68

01/08/2008 8:43:29 AM converter check - 1 20.68 0.07 0.66

01/08/2008 8:43:59 AM converter check - 1 20.68 0.07 0.64

01/08/2008 8:44:29 AM converter check - 1 20.7 0.06 0.77

01/08/2008 8:44:59 AM converter check - 1 20.69 0.07 0.72

01/08/2008 8:45:29 AM converter check - 1 20.69 0.07 0.66

01/08/2008 8:45:59 AM converter check - 1 20.69 0.06 0.75

01/08/2008 8:46:29 AM converter check - 1 20.69 0.05 0.58

01/08/2008 8:46:59 AM converter check - 2 20.7 0.06 0.48

01/08/2008 8:47:29 AM 20.71 0.07 0.49

01/08/2008 8:47:59 AM 20.69 0.06 0.62

01/08/2008 8:48:29 AM 20.74 0.04 0.7

01/08/2008 8:48:59 AM 19.76 7.01 -0.09

01/08/2008 8:49:29 AM 20.7 16.02 -0.24

01/08/2008 8:49:59 AM - ZERO 20.88 18.25 -0.24

01/08/2008 8:50:29 AM - ZERO 20.92 18.39 -0.24

01/08/2008 8:50:59 AM - ZERO 20.92 18.39 -0.24

01/08/2008 8:51:29 AM - ZERO 13.83 14.49 1.91

01/08/2008 8:51:59 AM - ZERO 0.37 0.91 3.92

01/08/2008 8:52:29 AM - ZERO 0.04 0.06 4.1

01/08/2008 8:52:59 AM - ZERO 0.03 0.04 4.06

01/08/2008 8:53:29 AM - ZERO 0.04 0.03 4.11

Page 5 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 8:53:59 AM - ZERO 0.02 0.02 4.06

01/08/2008 8:54:29 AM - ZERO 0.03 0.02 4.09

01/08/2008 8:54:59 AM - ZERO 4.47 0.03 3.74

01/08/2008 8:55:29 AM - ZERO 0.75 0.11 7.77

01/08/2008 8:55:59 AM - ZERO 0.03 0.01 8.01

01/08/2008 8:56:29 AM - Span 0.03 0.01 7.98

01/08/2008 8:56:59 AM - Span 0.03 0.01 7.96

01/08/2008 8:57:29 AM - Span 0.03 0 8

01/08/2008 8:57:59 AM - Span 0.06 0.07 4.42

01/08/2008 8:58:29 AM - Span 0.02 3.46 -0.04

01/08/2008 8:58:59 AM - Span 0.01 3.64 -0.14

01/08/2008 8:59:29 AM - Span 0.01 3.73 -0.15

01/08/2008 8:59:59 AM - Span 0.01 3.74 -0.14

01/08/2008 9:00:29 AM - Span 0 3.74 -0.14

01/08/2008 9:00:59 AM - Span 0.01 3.75 -0.16

01/08/2008 9:01:29 AM - Span 0.01 3.74 -0.15

01/08/2008 9:01:59 AM - Span 0.01 3.75 -0.16

01/08/2008 9:02:29 AM - Span 0.01 3.74 -0.07

01/08/2008 9:02:59 AM - Span 0.01 3.74 -0.17

01/08/2008 9:03:29 AM - Span 0.01 3.75 -0.15

01/08/2008 9:03:59 AM - Span 0.01 3.75 -0.14

01/08/2008 9:04:29 AM - Span 4.82 5.54 -0.07

01/08/2008 9:04:59 AM - Span 10.39 8.82 -0.02

01/08/2008 9:05:29 AM - Span 10.56 9.39 -0.03

01/08/2008 9:05:59 AM - Span 10.57 9.41 -0.01

01/08/2008 9:06:29 AM - Span 10.55 9.43 -0.05

01/08/2008 9:06:59 AM - Span 13.73 8.15 0.19

01/08/2008 9:07:29 AM - Span 20.96 0.17 0.6

01/08/2008 9:07:59 AM - Span 20.97 0.07 0.83

01/08/2008 9:08:29 AM - Span 20.93 0.06 0.85

01/08/2008 9:08:59 AM - Span 20.86 0.06 0.91

01/08/2008 9:09:29 AM - Span 17.49 1.45 0.28

01/08/2008 9:09:59 AM - Span 10.68 8.89 0

01/08/2008 9:10:29 AM - Span 10.52 9.37 -0.02

01/08/2008 9:10:59 AM - Span 10.53 9.39 -0.02

01/08/2008 9:11:29 AM - Span 10.53 9.4 0.04

01/08/2008 9:11:59 AM - Span 19.7 2.35 0.63

01/08/2008 9:12:29 AM - Span 17.81 0.31 0.25

01/08/2008 9:12:59 AM - Span 0.08 3.7 -0.11

01/08/2008 9:13:29 AM - Span 0.02 3.74 -0.1

Page 6 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 9:13:59 AM - Span 0.02 3.76 -0.06

01/08/2008 9:14:29 AM - Span 17.33 1.13 0.91

01/08/2008 9:14:59 AM - Span 20.87 0.07 1.12

01/08/2008 9:15:29 AM - Span 20.85 0.06 0.7

01/08/2008 9:15:59 AM - Span 18.19 0.55 0.38

01/08/2008 9:16:29 AM - Span 20.87 0.08 0.3

01/08/2008 9:16:59 AM - Span 20.93 0.06 0.26

01/08/2008 9:17:29 AM - Span 20.96 0.04 0.27

01/08/2008 9:17:59 AM - Span 14.43 4.23 0.03

01/08/2008 9:18:29 AM - Span 10.63 9.16 -0.01

01/08/2008 9:18:59 AM - ZERO 10.59 9.35 -0.01

01/08/2008 9:19:29 AM - ZERO 10.57 9.37 -0.02

01/08/2008 9:19:59 AM - Span 10.57 9.38 -0.01

01/08/2008 9:20:29 AM - Span 10.56 9.39 0.58

01/08/2008 9:20:59 AM - Span 1.69 2.7 7.06

01/08/2008 9:21:29 AM - Span 0.07 0.08 7.97

01/08/2008 9:21:59 AM - ZERO 0.05 0.04 7.99

01/08/2008 9:22:29 AM - ZERO 0.05 0.03 7.99

01/08/2008 9:22:59 AM - Span 0.05 0.03 7.99

01/08/2008 9:23:29 AM - Span 0.04 0.02 8.01

01/08/2008 9:23:59 AM - Span 0.04 0.02 7.43

01/08/2008 9:24:29 AM - Span 17.89 0.07 1.18

01/08/2008 9:24:59 AM - Span 20.92 0.07 0.29

01/08/2008 9:25:29 AM - Span 20.95 0.06 0.29

01/08/2008 9:25:59 AM - Span 20.96 0.06 0.28

01/08/2008 9:26:29 AM - Span 9.03 0.53 0.95

01/08/2008 9:26:59 AM - Span 0.09 3.67 -0.09

01/08/2008 9:27:29 AM - Span 0.05 3.7 -0.1

01/08/2008 9:27:59 AM - Span 0.04 3.73 -0.11

01/08/2008 9:28:29 AM - Span 0.04 3.73 -0.1

01/08/2008 9:28:59 AM - Span 0.02 3.74 -0.1

01/08/2008 9:29:29 AM - Span 0.01 3.74 -0.11

01/08/2008 9:29:59 AM - Span 0.03 3.73 -0.11

01/08/2008 9:30:29 AM - Span 0.02 3.74 -0.12

01/08/2008 9:30:59 AM - Span 0.02 3.73 -0.11

01/08/2008 9:31:29 AM - Span 0.02 3.73 -0.09

01/08/2008 9:31:59 AM - Span 0.03 3.73 -0.11

01/08/2008 9:32:29 AM - Span 0.02 3.73 -0.1

01/08/2008 9:32:59 AM - Span 0.03 3.74 -0.12

01/08/2008 9:33:29 AM - Span 0.02 3.73 -0.1

Page 7 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 9:33:59 AM - Span 0.03 3.73 -0.12

01/08/2008 9:34:29 AM - Span 0.03 3.74 -0.12

01/08/2008 9:34:59 AM - Span 0.03 3.73 -0.11

01/08/2008 9:35:29 AM - Span 0.02 3.73 -0.12

01/08/2008 9:35:59 AM - Span 0.02 3.74 -0.1

01/08/2008 9:36:29 AM - Span 0.17 3.74 -0.04

01/08/2008 9:36:59 AM - Span 20.31 0.33 0.27

01/08/2008 9:37:29 AM - Span 20.92 0.08 0.29

01/08/2008 9:37:59 AM - Span 20.94 0.07 0.3

01/08/2008 9:38:29 AM - Span 20.94 0.06 0.3

01/08/2008 9:38:59 AM - Span 20.95 0.06 0.3

01/08/2008 9:39:29 AM - Span 20.96 0.05 0.31

01/08/2008 9:39:59 AM - Span 20.95 0.06 0.3

01/08/2008 9:40:29 AM - Span 20.95 0.05 0.29

01/08/2008 9:40:59 AM - Span 20.95 0.05 0.29

01/08/2008 9:41:29 AM - Span 20.96 0.04 0.31

01/08/2008 9:41:59 AM - Span 20.97 0.05 0.29

01/08/2008 9:42:29 AM - Span 20.97 0.04 0.3

01/08/2008 9:42:59 AM - Span 20.97 0.05 0.28

01/08/2008 9:43:29 AM - Span 20.96 0.04 0.28

01/08/2008 9:43:59 AM - Span 20.96 0.04 0.3

01/08/2008 9:44:29 AM - Span 20.96 0.04 0.31

01/08/2008 9:44:59 AM - Span 20.97 0.05 0.32

01/08/2008 9:45:29 AM - Span 20.97 0.05 0.29

01/08/2008 9:45:59 AM - Span 20.98 0.05 0.3

01/08/2008 9:46:29 AM - Span 20.98 0.05 0.3

01/08/2008 9:46:59 AM - Span 20.97 0.04 0.3

01/08/2008 9:47:29 AM - Span 20.96 0.05 0.34

01/08/2008 9:47:59 AM - Span 20.98 0.05 0.31

01/08/2008 9:48:29 AM - Span 20.97 0.05 0.32

01/08/2008 9:48:59 AM - Span 20.96 0.05 0.3

01/08/2008 9:49:29 AM - Span 20.98 0.04 0.31

01/08/2008 9:49:59 AM - Span 20.98 0.05 0.28

01/08/2008 9:50:29 AM - Span 20.97 0.05 0.29

01/08/2008 9:50:59 AM - Span 20.99 0.05 0.28

01/08/2008 9:51:29 AM - Span 20.99 0.05 0.29

01/08/2008 9:51:59 AM - Span 20.99 0.05 0.31

01/08/2008 9:52:29 AM - Span 20.98 0.05 0.28

01/08/2008 9:52:59 AM - Span 20.98 0.06 0.3

01/08/2008 9:53:29 AM - Span 20.98 0.05 0.28

Page 8 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 9:53:59 AM - Span 20.99 0.05 0.29

01/08/2008 9:54:29 AM - Span 20.99 0.05 0.29

01/08/2008 9:54:59 AM - Span 20.98 0.04 0.29

01/08/2008 9:55:29 AM - Span 20.98 0.05 0.28

01/08/2008 9:55:59 AM - Span 20.98 0.04 0.28

01/08/2008 9:56:29 AM - Span 20.97 0.05 0.31

01/08/2008 9:56:59 AM - Span 20.99 0.06 0.3

01/08/2008 9:57:29 AM - Span 20.98 0.06 0.29

01/08/2008 9:57:59 AM - Span 20.98 0.05 0.27

01/08/2008 9:58:29 AM - Span 20.98 0.05 0.29

01/08/2008 9:58:59 AM - Span 20.98 0.05 0.32

01/08/2008 9:59:29 AM - Span 20.98 0.05 0.3

01/08/2008 9:59:59 AM - Span 20.98 0.05 0.29

01/08/2008 10:00:29 AM - Span 20.98 0.05 0.28

01/08/2008 10:00:59 AM - Span 20.97 0.05 0.28

01/08/2008 10:01:29 AM - Span 20.98 0.05 0.29

01/08/2008 10:01:59 AM - Span 20.98 0.05 0.28

01/08/2008 10:02:29 AM - Span 20.98 0.05 0.31

01/08/2008 10:02:59 AM - Span 20.98 0.05 0.27

01/08/2008 10:03:29 AM - Span 20.98 0.05 0.3

01/08/2008 10:03:59 AM - Span 20.98 0.05 0.28

01/08/2008 10:04:29 AM - Span 20.97 0.06 0.33

01/08/2008 10:04:59 AM - Span 20.97 0.05 0.29

01/08/2008 10:05:29 AM - Span 20.97 0.06 0.29

01/08/2008 10:05:59 AM - Span 20.98 0.06 0.31

01/08/2008 10:06:29 AM - Span 20.97 0.05 0.3

01/08/2008 10:06:59 AM - Span 20.97 0.04 0.31

01/08/2008 10:07:29 AM - Span 20.98 0.05 0.28

01/08/2008 10:07:59 AM - Span 20.97 0.06 0.31

01/08/2008 10:08:29 AM - Span 20.96 0.06 0.28

01/08/2008 10:08:59 AM - Span 20.98 0.05 0.29

01/08/2008 10:09:29 AM - Span 20.98 0.05 0.31

01/08/2008 10:09:59 AM - Span 20.97 0.05 0.3

01/08/2008 10:10:29 AM - Span 20.97 0.06 0.32

01/08/2008 10:10:59 AM - Span 20.96 0.06 0.3

01/08/2008 10:11:29 AM - Span 20.97 0.05 0.3

01/08/2008 10:11:59 AM - Span 20.98 0.05 0.33

01/08/2008 10:12:29 AM - Span 20.98 0.05 0.3

01/08/2008 10:12:59 AM - Span 20.99 0.06 0.3

01/08/2008 10:13:29 AM - Span 20.98 0.05 0.32

Page 9 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 10:13:59 AM - Span 20.99 0.05 0.31

01/08/2008 10:14:29 AM - Span 20.99 0.04 0.27

01/08/2008 10:14:59 AM - Span 20.99 0.04 0.32

01/08/2008 10:15:29 AM - Span 20.98 0.04 0.29

01/08/2008 10:15:59 AM - Span 20.98 0.05 0.3

01/08/2008 10:16:29 AM - Span 20.99 0.04 0.32

01/08/2008 10:16:59 AM - Span 20.99 0.05 0.3

01/08/2008 10:17:29 AM - Span 20.98 0.04 0.32

01/08/2008 10:17:59 AM - Span 20.99 0.05 0.29

01/08/2008 10:18:29 AM - Span 20.98 0.05 0.32

01/08/2008 10:18:59 AM - Span 20.98 0.05 0.32

01/08/2008 10:19:29 AM - Span 20.99 0.05 0.28

01/08/2008 10:19:59 AM - Span 20.98 0.04 0.31

01/08/2008 10:20:29 AM - Span 20.98 0.05 0.29

01/08/2008 10:20:59 AM - Span 20.99 0.04 0.3

01/08/2008 10:21:29 AM - Span 20.99 0.04 0.29

01/08/2008 10:21:59 AM - Span 20.98 0.05 0.31

01/08/2008 10:22:29 AM - Span 20.98 0.04 0.31

01/08/2008 10:22:59 AM - Span 20.99 0.05 0.31

01/08/2008 10:23:29 AM - Span 20.98 0.05 0.31

01/08/2008 10:23:59 AM - Span 20.98 0.04 0.3

01/08/2008 10:24:29 AM - Span 20.99 0.05 0.31

01/08/2008 10:24:59 AM - Span 20.99 0.05 0.29

01/08/2008 10:25:29 AM - Span 20.98 0.05 0.32

01/08/2008 10:25:59 AM - Span 20.98 0.06 0.35

01/08/2008 10:26:29 AM - Span 20.97 0.06 0.32

01/08/2008 10:26:59 AM - Span 20.97 0.05 0.32

01/08/2008 10:27:29 AM - Span 20.97 0.04 0.3

01/08/2008 10:27:59 AM - Span 20.97 0.06 0.33

01/08/2008 10:28:29 AM - Span 20.98 0.06 0.3

01/08/2008 10:28:59 AM - Span 20.97 0.04 0.29

01/08/2008 10:29:29 AM - Span 20.98 0.04 0.34

01/08/2008 10:29:59 AM - Span 20.98 0.05 0.29

01/08/2008 10:30:29 AM - Span 20.98 0.04 0.31

01/08/2008 10:30:59 AM - Span 20.95 0.06 0.39

01/08/2008 10:31:29 AM - Span 20.97 0.05 0.31

01/08/2008 10:31:59 AM - Span 20.98 0.05 0.32

01/08/2008 10:32:29 AM - Span 20.98 0.05 0.31

01/08/2008 10:32:59 AM - Span 20.97 0.05 0.3

01/08/2008 10:33:29 AM - Span 20.98 0.05 0.29

Page 10 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 10:33:59 AM - Span 20.97 0.05 0.32

01/08/2008 10:34:29 AM - Span 20.99 0.05 0.31

01/08/2008 10:34:59 AM - Span 20.99 0.04 0.33

01/08/2008 10:35:29 AM - Span 20.98 0.04 0.33

01/08/2008 10:35:59 AM - Span 20.98 0.05 0.32

01/08/2008 10:36:29 AM - Span 20.99 0.04 0.31

01/08/2008 10:36:59 AM - Span 20.97 0.05 0.33

01/08/2008 10:37:29 AM - Span 20.98 0.05 0.33

01/08/2008 10:37:59 AM - Span 20.98 0.04 0.34

01/08/2008 10:38:29 AM - Span 20.97 0.04 0.33

01/08/2008 10:38:59 AM 20.98 0.05 0.32

01/08/2008 10:39:29 AM 20.97 0.03 0.31

01/08/2008 10:39:59 AM 20.99 0.04 0.32

01/08/2008 10:40:29 AM 20.98 0.05 0.3

01/08/2008 10:40:59 AM 19.51 0.44 3.74

01/08/2008 10:41:29 AM 12.02 8.74 6.16

01/08/2008 10:41:59 AM 11.63 9.66 6.16

01/08/2008 10:42:29 AM 11.63 9.66 6.15

01/08/2008 10:42:59 AM 11.63 9.67 6.18

01/08/2008 10:43:29 AM 11.63 9.69 6.15

01/08/2008 10:43:59 AM 11.64 9.69 6.05

01/08/2008 10:44:29 AM 11.64 9.65 6.23

01/08/2008 10:44:59 AM 11.62 9.69 6.16

01/08/2008 10:45:29 AM 11.63 9.67 6.25

01/08/2008 10:45:59 AM 11.63 9.68 6.24

01/08/2008 10:46:29 AM Traverse - 1 11.61 9.69 6.23

01/08/2008 10:46:59 AM Traverse - 1 11.61 9.7 6.26

01/08/2008 10:47:29 AM Traverse - 1 11.61 9.69 6.26

01/08/2008 10:47:59 AM Traverse - 1 11.59 9.68 6.32

01/08/2008 10:48:29 AM Traverse - 1 11.61 9.69 6.25

01/08/2008 10:48:59 AM Traverse - 1 11.6 9.7 6.32

01/08/2008 10:49:29 AM Traverse - 1 11.59 9.69 6.32

01/08/2008 10:49:59 AM Traverse - 1 11.61 9.7 6.46

01/08/2008 10:50:29 AM Traverse - 1 11.52 9.69 6.93

01/08/2008 10:50:59 AM Traverse - 1 11.51 9.73 6.67

01/08/2008 10:51:29 AM Traverse - 1 11.56 9.69 6.5

01/08/2008 10:51:59 AM Traverse - 1 11.6 9.69 6.38

01/08/2008 10:52:29 AM Traverse - 1 11.59 9.71 6.36

01/08/2008 10:52:59 AM Traverse - 1 11.6 9.71 6.31

01/08/2008 10:53:29 AM Traverse - 1 11.61 9.69 6.37

Page 11 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 10:53:59 AM Traverse - 1 11.61 9.7 6.24

01/08/2008 10:54:29 AM Traverse - 1 11.62 9.69 6.25

01/08/2008 10:54:59 AM Traverse - 1 11.61 9.7 6.13

01/08/2008 10:55:29 AM Traverse - 1 11.62 9.74 6.05

01/08/2008 10:55:59 AM Traverse - 1 11.61 9.7 6.3

01/08/2008 10:56:29 AM Traverse - 1 11.6 9.7 6.15

01/08/2008 10:56:59 AM Traverse - 1 11.61 9.7 6.31

01/08/2008 10:57:29 AM Traverse - 1 11.59 9.72 6.29

01/08/2008 10:57:59 AM Traverse - 1 11.59 9.7 6.45

01/08/2008 10:58:29 AM Traverse - 1 11.57 9.72 6.39

01/08/2008 10:58:59 AM Traverse - 1 11.57 9.71 6.45

01/08/2008 10:59:29 AM Traverse - 1 11.59 9.69 6.29

01/08/2008 10:59:59 AM Traverse - 1 11.62 9.69 6.09

01/08/2008 11:00:29 AM Traverse - 1 11.61 9.7 6.26

01/08/2008 11:00:59 AM Traverse - 1 11.61 9.69 6.3

01/08/2008 11:01:29 AM Traverse - 1 11.61 9.69 6.27

01/08/2008 11:01:59 AM Traverse - 1 11.59 9.69 6.29

01/08/2008 11:02:29 AM Traverse - 1 11.59 9.68 6.43

01/08/2008 11:02:59 AM Traverse - 1 11.57 9.69 6.51

01/08/2008 11:03:29 AM Traverse - 1 11.57 9.68 6.54

01/08/2008 11:03:59 AM Traverse - 1 11.57 9.69 6.59

01/08/2008 11:04:29 AM Traverse - 1 11.56 9.67 6.52

01/08/2008 11:04:59 AM Traverse - 1 11.56 9.68 6.58

01/08/2008 11:05:29 AM Run Paused 11.5 9.69 6.92

01/08/2008 11:05:59 AM Run Paused 11.49 9.7 6.85

01/08/2008 11:06:29 AM Run Paused 13.9 8.79 2.19

01/08/2008 11:06:59 AM Run Paused 20.89 0.29 0.35

01/08/2008 11:07:29 AM Run Paused 20.94 0.14 0.37

01/08/2008 11:07:59 AM Run Paused 20.95 0.1 0.41

01/08/2008 11:08:29 AM Run Paused 20.95 0.11 0.42

01/08/2008 11:08:59 AM Run Paused 18.79 0.99 4.32

01/08/2008 11:09:29 AM Run Paused 11.84 8.92 6.69

01/08/2008 11:09:59 AM Run Paused 11.57 9.63 6.73

01/08/2008 11:10:29 AM Run Paused 11.56 9.66 6.81

01/08/2008 11:10:59 AM Run Paused 11.54 9.69 6.87

01/08/2008 11:11:29 AM Run Paused 11.53 9.68 6.73

01/08/2008 11:11:59 AM Run Paused 11.54 9.67 6.77

01/08/2008 11:12:29 AM Run Paused 11.54 9.66 7.08

01/08/2008 11:12:59 AM Run Paused 11.5 9.7 7.07

01/08/2008 11:13:29 AM Traverse - 1 11.52 9.7 7

Page 12 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 11:13:59 AM Traverse - 1 11.53 9.69 6.83

01/08/2008 11:14:29 AM Traverse - 1 11.53 9.7 6.87

01/08/2008 11:14:59 AM Traverse - 1 11.52 9.69 6.94

01/08/2008 11:15:29 AM Traverse - 1 11.47 9.71 7.25

01/08/2008 11:15:59 AM Traverse - 1 11.45 9.7 7.21

01/08/2008 11:16:29 AM Traverse - 1 11.51 9.69 6.94

01/08/2008 11:16:59 AM Traverse - 1 11.55 9.7 6.74

01/08/2008 11:17:29 AM Traverse - 1 11.56 9.7 6.59

01/08/2008 11:17:59 AM Traverse - 1 11.56 9.69 6.53

01/08/2008 11:18:29 AM Traverse - 1 11.58 9.69 6.54

01/08/2008 11:18:59 AM Traverse - 1 11.57 9.69 6.57

01/08/2008 11:19:29 AM Traverse - 1 11.58 9.67 6.55

01/08/2008 11:19:59 AM Traverse - 1 11.57 9.66 6.49

01/08/2008 11:20:29 AM Traverse - 1 11.57 9.67 6.47

01/08/2008 11:20:59 AM Traverse - 1 11.56 9.7 6.51

01/08/2008 11:21:29 AM Traverse - 1 11.57 9.71 6.43

01/08/2008 11:21:59 AM Traverse - 1 11.55 9.71 6.38

01/08/2008 11:22:29 AM Traverse - 1 11.58 9.71 6.38

01/08/2008 11:22:59 AM Traverse - 1 11.57 9.7 6.48

01/08/2008 11:23:29 AM Traverse - 1 11.56 9.71 6.42

01/08/2008 11:23:59 AM Traverse - 1 11.56 9.7 6.49

01/08/2008 11:24:29 AM Traverse - 1 11.57 9.7 6.48

01/08/2008 11:24:59 AM Traverse - 1 11.57 9.71 6.31

01/08/2008 11:25:29 AM Traverse - 1 11.57 9.7 6.31

01/08/2008 11:25:59 AM Traverse - 1 11.6 9.7 6.25

01/08/2008 11:26:29 AM Traverse - 1 11.59 9.7 6.32

01/08/2008 11:26:59 AM Traverse - 1 11.59 9.68 6.42

01/08/2008 11:27:29 AM Traverse - 1 11.57 9.67 6.43

01/08/2008 11:27:59 AM Traverse - 1 11.59 9.7 6.3

01/08/2008 11:28:29 AM Traverse - 1 11.59 9.68 6.37

01/08/2008 11:28:59 AM Traverse - 1 11.57 9.68 6.35

01/08/2008 11:29:29 AM Traverse - 1 11.53 9.71 5.71

01/08/2008 11:29:59 AM Traverse - 1 11.53 9.69 6.61

01/08/2008 11:30:29 AM Traverse - 1 11.48 9.7 7.02

01/08/2008 11:30:59 AM Traverse - 1 11.47 9.71 6.66

01/08/2008 11:31:29 AM Traverse - 1 11.54 9.7 6.49

01/08/2008 11:31:59 AM Run Paused 11.55 9.69 6.47

01/08/2008 11:32:29 AM Run Paused 11.55 9.68 6.51

01/08/2008 11:32:59 AM Run Paused 11.54 9.67 6.64

01/08/2008 11:33:29 AM Run Paused 11.55 9.68 6.58

Page 13 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 11:33:59 AM Run Paused 16.06 6.95 2.01

01/08/2008 11:34:29 AM Run Paused 18.02 1.92 4.42

01/08/2008 11:34:59 AM Run Paused 11.77 9.12 6.48

01/08/2008 11:35:29 AM Run Paused 11.57 9.66 6.47

01/08/2008 11:35:59 AM Run Paused 11.57 9.66 6.56

01/08/2008 11:36:29 AM Run Paused 11.58 9.68 6.57

01/08/2008 11:36:59 AM Run Paused 11.58 9.71 6.41

01/08/2008 11:37:29 AM Traverse - 1 11.58 9.68 6.34

01/08/2008 11:37:59 AM Traverse - 1 11.58 9.69 6.39

01/08/2008 11:38:29 AM Traverse - 1 11.6 9.69 6.28

01/08/2008 11:38:59 AM Traverse - 1 11.59 9.7 6.34

01/08/2008 11:39:29 AM Traverse - 1 11.59 9.68 6.39

01/08/2008 11:39:59 AM Traverse - 1 11.59 9.7 6.36

01/08/2008 11:40:29 AM Traverse - 1 11.57 9.7 6.41

01/08/2008 11:40:59 AM Traverse - 1 11.58 9.69 6.45

01/08/2008 11:41:29 AM Traverse - 1 11.58 9.7 6.47

01/08/2008 11:41:59 AM Traverse - 1 11.58 9.7 6.49

01/08/2008 11:42:29 AM Traverse - 1 11.57 9.68 6.56

01/08/2008 11:42:59 AM Traverse - 1 11.6 9.69 6.35

01/08/2008 11:43:29 AM Traverse - 1 11.59 9.67 6.45

01/08/2008 11:43:59 AM Traverse - 1 11.57 9.69 6.45

01/08/2008 11:44:29 AM Traverse - 1 11.57 9.7 6.36

01/08/2008 11:44:59 AM Traverse - 1 11.59 9.69 6.33

01/08/2008 11:45:29 AM Traverse - 1 11.53 9.66 6.87

01/08/2008 11:45:59 AM Traverse - 1 11.51 9.71 6.95

01/08/2008 11:46:29 AM Traverse - 1 11.54 9.71 6.57

01/08/2008 11:46:59 AM Traverse - 1 11.56 9.68 6.52

01/08/2008 11:47:29 AM Traverse - 1 11.57 9.68 6.46

01/08/2008 11:47:59 AM Traverse - 1 11.58 9.7 6.4

01/08/2008 11:48:29 AM Traverse - 1 11.6 9.69 6.32

01/08/2008 11:48:59 AM Traverse - 1 11.57 9.7 6.38

01/08/2008 11:49:29 AM Traverse - 1 11.59 9.69 6.33

01/08/2008 11:49:59 AM Traverse - 1 11.57 9.69 6.41

01/08/2008 11:50:29 AM Traverse - 1 11.57 9.68 6.5

01/08/2008 11:50:59 AM Traverse - 1 11.55 9.69 6.57

01/08/2008 11:51:29 AM Traverse - 1 11.58 9.7 6.52

01/08/2008 11:51:59 AM Traverse - 1 11.58 9.72 6.32

01/08/2008 11:52:29 AM Traverse - 1 11.6 9.72 6.32

01/08/2008 11:52:59 AM Traverse - 1 11.58 9.71 6.44

01/08/2008 11:53:29 AM Traverse - 1 11.6 9.71 6.33

Page 14 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 11:53:59 AM Traverse - 1 11.6 9.72 6.39

01/08/2008 11:54:29 AM Traverse - 1 11.6 9.74 6.24

01/08/2008 11:54:59 AM Traverse - 1 11.6 9.72 6.43

01/08/2008 11:55:29 AM Traverse - 1 11.53 9.72 6.84

01/08/2008 11:55:59 AM Traverse - 1 11.51 9.74 6.77

01/08/2008 11:56:29 AM Run Paused 11.56 9.74 6.5

01/08/2008 11:56:59 AM Run Paused 11.59 9.73 6.41

01/08/2008 11:57:29 AM Run Paused 11.6 9.73 6.5

01/08/2008 11:57:59 AM Run Paused 12.02 9.69 3.55

01/08/2008 11:58:29 AM Run Paused 19.81 0.69 3.17

01/08/2008 11:58:59 AM Run Paused 12.04 8.73 6.18

01/08/2008 11:59:29 AM Run Paused 11.61 9.68 6.46

01/08/2008 11:59:59 AM Run Paused 11.6 9.7 6.37

01/08/2008 12:00:29 PM Run Paused 11.6 9.69 6.46

01/08/2008 12:00:59 PM Run Paused 11.57 9.71 6.58

01/08/2008 12:01:29 PM Traverse - 1 11.58 9.7 6.59

01/08/2008 12:01:59 PM Traverse - 1 11.58 9.69 6.53

01/08/2008 12:02:29 PM Traverse - 1 11.58 9.72 6.43

01/08/2008 12:02:59 PM Traverse - 1 11.58 9.7 6.55

01/08/2008 12:03:29 PM Traverse - 1 11.6 9.7 6.44

01/08/2008 12:03:59 PM Traverse - 1 11.59 9.73 6.35

01/08/2008 12:04:29 PM Traverse - 1 11.59 9.71 6.38

01/08/2008 12:04:59 PM Traverse - 1 11.6 9.69 6.31

01/08/2008 12:05:29 PM Traverse - 1 11.59 9.7 6.37

01/08/2008 12:05:59 PM Traverse - 1 11.59 9.72 6.42

01/08/2008 12:06:29 PM Traverse - 1 11.59 9.7 6.5

01/08/2008 12:06:59 PM Traverse - 1 11.59 9.72 6.34

01/08/2008 12:07:29 PM Traverse - 1 11.58 9.69 6.52

01/08/2008 12:07:59 PM Traverse - 1 11.57 9.69 6.48

01/08/2008 12:08:29 PM Traverse - 1 11.6 9.69 6.44

01/08/2008 12:08:59 PM Traverse - 1 11.58 9.68 6.55

01/08/2008 12:09:29 PM Traverse - 1 11.59 9.7 6.47

01/08/2008 12:09:59 PM Traverse - 1 11.57 9.68 6.58

01/08/2008 12:10:29 PM Traverse - 1 11.51 9.69 6.82

01/08/2008 12:10:59 PM Traverse - 1 11.53 9.72 6.56

01/08/2008 12:11:29 PM Traverse - 1 11.56 9.7 6.47

01/08/2008 12:11:59 PM Traverse - 1 11.59 9.7 6.34

01/08/2008 12:12:29 PM Traverse - 1 11.6 9.69 6.29

01/08/2008 12:12:59 PM Traverse - 1 11.59 9.69 6.3

01/08/2008 12:13:29 PM Traverse - 1 11.6 9.7 6.28

Page 15 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 12:13:59 PM Traverse - 1 11.57 9.68 6.44

01/08/2008 12:14:29 PM Traverse - 1 11.6 9.66 6.42

01/08/2008 12:14:59 PM Traverse - 1 11.61 9.68 6.4

01/08/2008 12:15:29 PM Traverse - 1 11.59 9.69 6.4

01/08/2008 12:15:59 PM Traverse - 1 11.57 9.72 6.5

01/08/2008 12:16:29 PM Traverse - 1 11.58 9.68 6.55

01/08/2008 12:16:59 PM Traverse - 1 11.59 9.69 6.32

01/08/2008 12:17:29 PM Traverse - 1 11.61 9.67 6.34

01/08/2008 12:17:59 PM Traverse - 1 11.6 9.71 6.26

01/08/2008 12:18:29 PM Traverse - 1 11.62 9.67 6.2

01/08/2008 12:18:59 PM Traverse - 1 11.59 9.71 6.22

01/08/2008 12:19:29 PM Traverse - 1 11.59 9.68 6.4

01/08/2008 12:19:59 PM Traverse - 1 11.58 9.68 6.65

01/08/2008 12:20:29 PM 11.56 9.7 6.67

01/08/2008 12:20:59 PM 11.56 9.69 5.29

01/08/2008 12:21:29 PM 10.12 8.5 0.29

01/08/2008 12:21:59 PM 10.56 9.39 0.03

01/08/2008 12:22:29 PM 10.56 9.41 0.03

01/08/2008 12:22:59 PM - ZERO 10.56 9.41 0.03

01/08/2008 12:23:29 PM - ZERO 10.56 9.4 0.02

01/08/2008 12:23:59 PM - ZERO 10.57 9.41 0.05

01/08/2008 12:24:29 PM - ZERO 10.56 9.4 0.02

01/08/2008 12:24:59 PM - ZERO 10.56 9.4 0.04

01/08/2008 12:25:29 PM - ZERO 8.01 8.43 4.42

01/08/2008 12:25:59 PM - ZERO 0.17 0.34 7.91

01/08/2008 12:26:29 PM - Span 0.09 0.1 8

01/08/2008 12:26:59 PM - ZERO 0.07 0.07 7.99

01/08/2008 12:27:29 PM - ZERO 0.08 0.06 7.16

01/08/2008 12:27:59 PM - ZERO 0.06 2.71 0.52

01/08/2008 12:28:29 PM - ZERO 0.04 3.73 -0.04

01/08/2008 12:28:59 PM - ZERO 0.05 3.75 -0.07

01/08/2008 12:29:29 PM - Span 0.05 3.76 -0.05

01/08/2008 12:29:59 PM - Span 0.05 3.76 -0.07

01/08/2008 12:30:29 PM - Span 0.05 3.75 -0.06

01/08/2008 12:30:59 PM - Span 0.04 3.75 -0.08

01/08/2008 12:31:29 PM - Span 0.04 3.75 -0.08

01/08/2008 12:31:59 PM - Span 0.04 3.75 -0.09

01/08/2008 12:32:29 PM - Span 0.04 3.74 -0.1

01/08/2008 12:32:59 PM - Span 0.04 3.75 -0.11

01/08/2008 12:33:29 PM - Span 0.04 3.75 -0.11

Page 16 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 12:33:59 PM - Span 0.05 3.74 -0.09

01/08/2008 12:34:29 PM - Span 0.04 3.74 0.47

01/08/2008 12:34:59 PM - Span 9.12 7.84 5.87

01/08/2008 12:35:29 PM - Span 11.43 9.61 7.01

01/08/2008 12:35:59 PM - Span 11.45 9.68 6.89

01/08/2008 12:36:29 PM - Span 11.5 9.65 6.62

01/08/2008 12:36:59 PM - Span 11.54 9.65 6.5

01/08/2008 12:37:29 PM - Span 11.56 9.66 6.48

01/08/2008 12:37:59 PM - Span 11.57 9.65 6.37

01/08/2008 12:38:29 PM - Span 11.58 9.66 6.41

01/08/2008 12:38:59 PM - Span 11.58 9.69 6.34

01/08/2008 12:39:29 PM - Span 11.59 9.68 6.42

01/08/2008 12:39:59 PM Run 2 - 1 11.58 9.66 6.45

01/08/2008 12:40:29 PM Run 2 - 1 11.58 9.67 6.41

01/08/2008 12:40:59 PM Run 2 - 1 11.56 9.69 6.52

01/08/2008 12:41:29 PM Run 2 - 1 11.56 9.66 6.46

01/08/2008 12:41:59 PM Run 2 - 1 11.56 9.67 6.45

01/08/2008 12:42:29 PM Run 2 - 1 11.56 9.66 6.51

01/08/2008 12:42:59 PM Run 2 - 1 11.59 9.67 6.38

01/08/2008 12:43:29 PM Run 2 - 1 11.58 9.68 6.39

01/08/2008 12:43:59 PM Run 2 - 1 11.59 9.7 6.32

01/08/2008 12:44:29 PM Run 2 - 1 11.61 9.68 6.15

01/08/2008 12:44:59 PM Run 2 - 1 11.59 9.67 6.27

01/08/2008 12:45:29 PM Run 2 - 1 11.61 9.69 6.27

01/08/2008 12:45:59 PM Run 2 - 1 11.59 9.69 6.33

01/08/2008 12:46:29 PM Run 2 - 1 11.59 9.7 6.27

01/08/2008 12:46:59 PM Run 2 - 1 11.58 9.67 6.38

01/08/2008 12:47:29 PM Run 2 - 1 11.57 9.69 6.43

01/08/2008 12:47:59 PM Run 2 - 1 11.58 9.67 6.5

01/08/2008 12:48:29 PM Run 2 - 1 11.59 9.66 6.42

01/08/2008 12:48:59 PM Run 2 - 1 11.59 9.69 6.44

01/08/2008 12:49:29 PM Run 2 - 1 11.58 9.69 6.38

01/08/2008 12:49:59 PM Run 2 - 1 11.59 9.68 6.4

01/08/2008 12:50:29 PM Run 2 - 1 11.53 9.7 6.79

01/08/2008 12:50:59 PM Run 2 - 1 11.52 9.69 6.75

01/08/2008 12:51:29 PM Run 2 - 1 11.58 9.71 6.38

01/08/2008 12:51:59 PM Run 2 - 1 11.59 9.72 6.31

01/08/2008 12:52:29 PM Run 2 - 1 11.62 9.68 6.16

01/08/2008 12:52:59 PM Run 2 - 1 11.6 9.69 6.32

01/08/2008 12:53:29 PM Run 2 - 1 11.59 9.7 6.34

Page 17 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 12:53:59 PM Run 2 - 1 11.58 9.68 6.39

01/08/2008 12:54:29 PM Run 2 - 1 11.59 9.67 6.39

01/08/2008 12:54:59 PM Run 2 - 1 11.59 9.67 6.15

01/08/2008 12:55:29 PM Run 2 - 1 11.59 9.66 6.29

01/08/2008 12:55:59 PM Run 2 - 1 11.59 9.69 6.29

01/08/2008 12:56:29 PM Run 2 - 1 11.6 9.66 6.19

01/08/2008 12:56:59 PM Run 2 - 1 11.61 9.66 6.23

01/08/2008 12:57:29 PM Run 2 - 1 11.62 9.64 6.19

01/08/2008 12:57:59 PM Run 2 - 1 11.6 9.68 6.13

01/08/2008 12:58:29 PM Run 2 - 1 11.61 9.63 6.16

01/08/2008 12:58:59 PM Run 2 - 1 11.61 9.64 6.33

01/08/2008 12:59:29 PM Run 2 - 1 11.61 9.66 6.3

01/08/2008 12:59:59 PM Run 2 - 1 11.61 9.64 6.22

01/08/2008 1:00:29 PM Run 2 - 1 11.63 9.67 6.09

01/08/2008 1:00:59 PM 11.62 9.65 6.2

01/08/2008 1:01:29 PM 11.61 9.67 5.54

01/08/2008 1:01:59 PM 1.56 5.12 0.42

01/08/2008 1:02:29 PM 0.1 3.77 -0.17

01/08/2008 1:02:59 PM - Span 0.08 3.76 -0.14

01/08/2008 1:03:29 PM - ZERO 0.08 3.75 -0.15

01/08/2008 1:03:59 PM - ZERO 0.06 3.75 -0.16

01/08/2008 1:04:29 PM - ZERO 4.2 5.14 -0.08

01/08/2008 1:04:59 PM - ZERO 10.36 9.04 -0.06

01/08/2008 1:05:29 PM - Span 10.54 9.34 -0.02

01/08/2008 1:05:59 PM - ZERO 10.54 9.35 -0.04

01/08/2008 1:06:29 PM - ZERO 10.55 9.35 -0.03

01/08/2008 1:06:59 PM - ZERO 7.58 8.09 4.02

01/08/2008 1:07:29 PM - ZERO 0.17 0.31 7.83

01/08/2008 1:07:59 PM - ZERO 0.09 0.07 7.92

01/08/2008 1:08:29 PM - ZERO 0.07 0.05 7.91

01/08/2008 1:08:59 PM - ZERO 0.08 0.03 7.96

01/08/2008 1:09:29 PM - ZERO 5.59 3.93 6.64

01/08/2008 1:09:59 PM - ZERO 9.66 8.03 0.83

01/08/2008 1:10:29 PM - ZERO 11.39 8.16 -0.02

01/08/2008 1:10:59 PM - ZERO 10.55 9.33 -0.09

01/08/2008 1:11:29 PM - ZERO 10.54 9.35 -0.07

01/08/2008 1:11:59 PM - ZERO 10.7 9.36 2.98

01/08/2008 1:12:29 PM - ZERO 11.63 9.62 5.8

01/08/2008 1:12:59 PM - ZERO 11.6 9.61 6.1

01/08/2008 1:13:29 PM - ZERO 11.62 9.64 6.14

Page 18 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 1:13:59 PM - ZERO 11.64 9.64 6.04

01/08/2008 1:14:29 PM run 3 - 1 11.63 9.65 6.2

01/08/2008 1:14:59 PM run 3 - 1 11.64 9.69 6.04

01/08/2008 1:15:29 PM run 3 - 1 11.64 9.67 5.94

01/08/2008 1:15:59 PM run 3 - 1 11.6 9.66 6.31

01/08/2008 1:16:29 PM run 3 - 1 11.58 9.67 6.29

01/08/2008 1:16:59 PM run 3 - 1 11.61 9.66 6.14

01/08/2008 1:17:29 PM run 3 - 1 11.66 9.66 6

01/08/2008 1:17:59 PM run 3 - 1 11.65 9.65 6.03

01/08/2008 1:18:29 PM run 3 - 1 11.62 9.65 6.24

01/08/2008 1:18:59 PM run 3 - 1 11.63 9.63 6.08

01/08/2008 1:19:29 PM run 3 - 1 11.63 9.66 6.05

01/08/2008 1:19:59 PM run 3 - 1 11.64 9.63 6.05

01/08/2008 1:20:29 PM run 3 - 1 11.63 9.64 6.06

01/08/2008 1:20:59 PM run 3 - 1 11.64 9.63 6.04

01/08/2008 1:21:29 PM run 3 - 1 11.63 9.63 6.13

01/08/2008 1:21:59 PM run 3 - 1 11.61 9.65 6.05

01/08/2008 1:22:29 PM run 3 - 1 11.61 9.64 5.99

01/08/2008 1:22:59 PM run 3 - 1 11.61 9.64 5.91

01/08/2008 1:23:29 PM run 3 - 1 11.62 9.62 5.94

01/08/2008 1:23:59 PM run 3 - 1 11.62 9.62 6.18

01/08/2008 1:24:29 PM run 3 - 1 11.57 9.61 6.27

01/08/2008 1:24:59 PM run 3 - 1 11.6 9.61 6.29

01/08/2008 1:25:29 PM run 3 - 1 11.59 9.63 6.24

01/08/2008 1:25:59 PM run 3 - 1 11.59 9.61 6.22

01/08/2008 1:26:29 PM run 3 - 1 11.58 9.61 6.26

01/08/2008 1:26:59 PM run 3 - 1 11.57 9.62 6.22

01/08/2008 1:27:29 PM run 3 - 1 11.61 9.63 6.05

01/08/2008 1:27:59 PM run 3 - 1 11.6 9.64 6.08

01/08/2008 1:28:29 PM run 3 - 1 11.61 9.6 6.08

01/08/2008 1:28:59 PM run 3 - 1 11.61 9.65 6

01/08/2008 1:29:29 PM run 3 - 1 11.61 9.64 6.02

01/08/2008 1:29:59 PM run 3 - 1 11.61 9.65 6

01/08/2008 1:30:29 PM run 3 - 1 11.6 9.63 5.95

01/08/2008 1:30:59 PM run 3 - 1 11.53 9.63 5.69

01/08/2008 1:31:29 PM run 3 - 1 11.51 9.65 6.59

01/08/2008 1:31:59 PM run 3 - 1 11.56 9.63 6.41

01/08/2008 1:32:29 PM run 3 - 1 11.56 9.68 6.46

01/08/2008 1:32:59 PM run 3 - 1 11.57 9.67 6.31

01/08/2008 1:33:29 PM run 3 - 1 11.59 9.68 6.22

Page 19 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 1:33:59 PM run 3 - 1 11.58 9.69 6.31

01/08/2008 1:34:29 PM run 3 - 1 11.58 9.69 6.28

01/08/2008 1:34:59 PM run 3 - 1 11.59 9.71 6.25

01/08/2008 1:35:29 PM run 3 - 2 11.59 9.7 6.19

01/08/2008 1:35:59 PM 11.59 9.7 6.25

01/08/2008 1:36:29 PM 11.59 9.71 6.14

01/08/2008 1:36:59 PM 10.6 9.56 3.09

01/08/2008 1:37:29 PM 0.29 4.1 -0.09

01/08/2008 1:37:59 PM 0.1 3.84 -0.16

01/08/2008 1:38:29 PM - Span 0.08 3.8 -0.14

01/08/2008 1:38:59 PM - Span 0.07 3.8 -0.15

01/08/2008 1:39:29 PM - Span 0.07 3.79 -0.16

01/08/2008 1:39:59 PM - ZERO 0.08 3.78 -0.17

01/08/2008 1:40:29 PM - ZERO 0.07 3.8 -0.14

01/08/2008 1:40:59 PM - ZERO 0.06 3.78 -0.15

01/08/2008 1:41:29 PM - ZERO 5.44 5.81 -0.09

01/08/2008 1:41:59 PM - ZERO 10.43 9.16 -0.02

01/08/2008 1:42:29 PM - Span 10.51 9.35 -0.03

01/08/2008 1:42:59 PM - ZERO 10.52 9.35 -0.02

01/08/2008 1:43:29 PM - ZERO 10.54 9.38 -0.04

01/08/2008 1:43:59 PM - ZERO 10.53 9.38 -0.02

01/08/2008 1:44:29 PM - ZERO 7.36 7.97 3.88

01/08/2008 1:44:59 PM - ZERO 0.15 0.29 7.81

01/08/2008 1:45:29 PM - Span 0.07 0.1 7.95

01/08/2008 1:45:59 PM - ZERO 0.07 0.07 7.95

01/08/2008 1:46:29 PM - ZERO 7.18 5.49 1.86

01/08/2008 1:46:59 PM - ZERO 10.99 9.26 4.78

01/08/2008 1:47:29 PM - ZERO 11.43 9.44 6.43

01/08/2008 1:47:59 PM - ZERO 11.51 9.61 6.72

01/08/2008 1:48:29 PM - ZERO 11.51 9.63 6.71

01/08/2008 1:48:59 PM run 4 - 1 11.52 9.64 6.65

01/08/2008 1:49:29 PM run 4 - 1 11.52 9.64 6.59

01/08/2008 1:49:59 PM run 4 - 1 11.53 9.64 6.56

01/08/2008 1:50:29 PM run 4 - 1 11.54 9.65 6.52

01/08/2008 1:50:59 PM run 4 - 1 11.54 9.66 6.47

01/08/2008 1:51:29 PM run 4 - 1 11.55 9.65 6.39

01/08/2008 1:51:59 PM run 4 - 1 11.55 9.64 6.38

01/08/2008 1:52:29 PM run 4 - 1 11.55 9.63 6.44

01/08/2008 1:52:59 PM run 4 - 1 11.54 9.64 6.45

01/08/2008 1:53:29 PM run 4 - 1 11.53 9.64 6.42

Page 20 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 1:53:59 PM run 4 - 1 11.56 9.63 6.35

01/08/2008 1:54:29 PM run 4 - 1 11.57 9.62 6.33

01/08/2008 1:54:59 PM run 4 - 1 11.56 9.62 6.39

01/08/2008 1:55:29 PM run 4 - 1 11.52 9.62 6.68

01/08/2008 1:55:59 PM run 4 - 1 11.47 9.66 6.81

01/08/2008 1:56:29 PM run 4 - 1 11.52 9.66 6.38

01/08/2008 1:56:59 PM run 4 - 1 11.57 9.64 6.22

01/08/2008 1:57:29 PM run 4 - 1 11.57 9.64 6.19

01/08/2008 1:57:59 PM run 4 - 1 11.57 9.65 6.18

01/08/2008 1:58:29 PM run 4 - 1 11.57 9.64 6.27

01/08/2008 1:58:59 PM run 4 - 1 11.57 9.63 6.29

01/08/2008 1:59:29 PM run 4 - 1 11.57 9.64 6.21

01/08/2008 1:59:59 PM run 4 - 1 11.58 9.64 6.11

01/08/2008 2:00:29 PM run 4 - 1 11.55 9.63 6.28

01/08/2008 2:00:59 PM run 4 - 1 11.56 9.61 6.32

01/08/2008 2:01:29 PM run 4 - 1 11.55 9.65 6.35

01/08/2008 2:01:59 PM run 4 - 1 11.56 9.63 6.3

01/08/2008 2:02:29 PM run 4 - 1 11.57 9.64 6.19

01/08/2008 2:02:59 PM run 4 - 1 11.56 9.65 6.22

01/08/2008 2:03:29 PM run 4 - 1 11.58 9.66 6.08

01/08/2008 2:03:59 PM run 4 - 1 11.61 9.65 5.95

01/08/2008 2:04:29 PM run 4 - 1 11.6 9.65 5.98

01/08/2008 2:04:59 PM run 4 - 1 11.59 9.64 6.23

01/08/2008 2:05:29 PM run 4 - 1 11.58 9.65 6.19

01/08/2008 2:05:59 PM run 4 - 1 11.57 9.66 6.2

01/08/2008 2:06:29 PM run 4 - 1 11.55 9.66 6.27

01/08/2008 2:06:59 PM run 4 - 1 11.56 9.65 6.24

01/08/2008 2:07:29 PM run 4 - 1 11.58 9.65 6.12

01/08/2008 2:07:59 PM run 4 - 1 11.58 9.64 6.07

01/08/2008 2:08:29 PM run 4 - 1 11.59 9.64 6.19

01/08/2008 2:08:59 PM run 4 - 1 11.58 9.65 6.1

01/08/2008 2:09:29 PM run 4 - 1 11.59 9.62 6.17

01/08/2008 2:09:59 PM 11.59 9.64 6.16

01/08/2008 2:10:29 PM 8.06 8.25 3.89

01/08/2008 2:10:59 PM 0.11 3.82 -0.14

01/08/2008 2:11:29 PM - ZERO 0.06 3.76 -0.15

01/08/2008 2:11:59 PM - Span 0.05 3.75 -0.15

01/08/2008 2:12:29 PM - Span 0.04 3.76 -0.15

01/08/2008 2:12:59 PM - Span 0.03 3.74 -0.14

01/08/2008 2:13:29 PM - Span 0.04 3.74 0.04

Page 21 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 2:13:59 PM - ZERO 0.05 0.96 7.16

01/08/2008 2:14:29 PM - ZERO 0.05 0.06 7.92

01/08/2008 2:14:59 PM - ZERO 0.05 0.03 7.92

01/08/2008 2:15:29 PM - ZERO 0.04 0.03 7.91

01/08/2008 2:15:59 PM - ZERO 7.71 5.81 0.67

01/08/2008 2:16:29 PM - Span 10.46 9.17 0

01/08/2008 2:16:59 PM - ZERO 10.5 9.3 -0.03

01/08/2008 2:17:29 PM - ZERO 10.52 9.34 -0.08

01/08/2008 2:17:59 PM - ZERO 10.5 9.35 0.44

01/08/2008 2:18:29 PM - ZERO 11.22 9.49 5.11

01/08/2008 2:18:59 PM - ZERO 11.55 9.61 6.13

01/08/2008 2:19:29 PM - ZERO 11.59 9.62 6.06

01/08/2008 2:19:59 PM RUN5 - 1 11.58 9.63 6.01

01/08/2008 2:20:29 PM RUN5 - 1 11.58 9.63 6

01/08/2008 2:20:59 PM RUN5 - 1 11.59 9.63 5.96

01/08/2008 2:21:29 PM RUN5 - 1 11.57 9.62 6.18

01/08/2008 2:21:59 PM RUN5 - 1 11.58 9.63 6.02

01/08/2008 2:22:29 PM RUN5 - 1 11.59 9.62 6.02

01/08/2008 2:22:59 PM RUN5 - 1 11.59 9.62 6.08

01/08/2008 2:23:29 PM RUN5 - 1 11.58 9.62 6.09

01/08/2008 2:23:59 PM RUN5 - 1 11.58 9.62 6.15

01/08/2008 2:24:29 PM RUN5 - 1 11.57 9.63 6.12

01/08/2008 2:24:59 PM RUN5 - 1 11.58 9.62 6.21

01/08/2008 2:25:29 PM RUN5 - 1 11.55 9.64 6.45

01/08/2008 2:25:59 PM RUN5 - 1 11.51 9.65 6.5

01/08/2008 2:26:29 PM RUN5 - 1 11.53 9.65 6.42

01/08/2008 2:26:59 PM RUN5 - 1 11.55 9.64 6.27

01/08/2008 2:27:29 PM RUN5 - 1 11.55 9.64 6.27

01/08/2008 2:27:59 PM RUN5 - 1 11.56 9.65 6.21

01/08/2008 2:28:29 PM RUN5 - 1 11.57 9.65 6.12

01/08/2008 2:28:59 PM RUN5 - 1 11.58 9.66 6.09

01/08/2008 2:29:29 PM RUN5 - 1 11.57 9.63 6.14

01/08/2008 2:29:59 PM RUN5 - 1 11.57 9.64 6.2

01/08/2008 2:30:29 PM RUN5 - 1 11.58 9.66 5.81

01/08/2008 2:30:59 PM RUN5 - 1 11.55 9.67 5.44

01/08/2008 2:31:29 PM RUN5 - 1 11.53 9.7 6.06

01/08/2008 2:31:59 PM RUN5 - 1 11.57 9.68 6.11

01/08/2008 2:32:29 PM RUN5 - 1 11.55 9.67 6.08

01/08/2008 2:32:59 PM RUN5 - 1 11.58 9.65 6.11

01/08/2008 2:33:29 PM RUN5 - 1 11.56 9.66 6.22

Page 22 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 2:33:59 PM RUN5 - 1 11.54 9.68 6.37

01/08/2008 2:34:29 PM RUN5 - 1 11.54 9.66 6.46

01/08/2008 2:34:59 PM RUN5 - 1 11.54 9.69 6.26

01/08/2008 2:35:29 PM RUN5 - 1 11.53 9.67 6.72

01/08/2008 2:35:59 PM RUN5 - 1 11.47 9.71 6.66

01/08/2008 2:36:29 PM RUN5 - 1 11.5 9.65 6.45

01/08/2008 2:36:59 PM RUN5 - 1 11.55 9.63 6.25

01/08/2008 2:37:29 PM RUN5 - 1 11.56 9.62 6.19

01/08/2008 2:37:59 PM RUN5 - 1 11.57 9.63 6.08

01/08/2008 2:38:29 PM RUN5 - 1 11.56 9.63 6.24

01/08/2008 2:38:59 PM RUN5 - 1 11.56 9.63 6.18

01/08/2008 2:39:29 PM RUN5 - 1 11.57 9.62 6.12

01/08/2008 2:39:59 PM RUN5 - 1 11.55 9.62 6.17

01/08/2008 2:40:29 PM RUN5 - 1 11.57 9.59 6.27

01/08/2008 2:40:59 PM 11.55 9.63 6.16

01/08/2008 2:41:29 PM 11.53 9.61 4.73

01/08/2008 2:41:59 PM 3.36 6.19 0.08

01/08/2008 2:42:29 PM 0.06 3.77 -0.18

01/08/2008 2:42:59 PM 0.04 3.73 -0.17

01/08/2008 2:43:29 PM - Span 0.03 3.72 -0.17

01/08/2008 2:43:59 PM - Span 0.05 3.7 -0.18

01/08/2008 2:44:29 PM - Span 0.04 3.71 -0.16

01/08/2008 2:44:59 PM - ZERO 0.03 3.72 -0.19

01/08/2008 2:45:29 PM - ZERO 0.04 3.71 -0.12

01/08/2008 2:45:59 PM - ZERO 0.05 2.73 6.54

01/08/2008 2:46:29 PM - ZERO 0.04 0.05 7.9

01/08/2008 2:46:59 PM - Span 0.05 0.03 7.91

01/08/2008 2:47:29 PM - ZERO 0.05 0.01 7.9

01/08/2008 2:47:59 PM - ZERO 0.04 0 7.88

01/08/2008 2:48:29 PM - ZERO 0.03 0.86 1.38

01/08/2008 2:48:59 PM - Span 0.03 3.59 -0.14

01/08/2008 2:49:29 PM - Span 0.03 3.65 -0.19

01/08/2008 2:49:59 PM - Span 0.34 3.66 -0.1

01/08/2008 2:50:29 PM - Span 9.6 8.29 -0.05

01/08/2008 2:50:59 PM - Span 10.5 9.22 -0.05

01/08/2008 2:51:29 PM - ZERO 10.52 9.24 -0.08

01/08/2008 2:51:59 PM - ZERO 10.51 9.28 -0.06

01/08/2008 2:52:29 PM - ZERO 10.51 9.3 -0.08

01/08/2008 2:52:59 PM - ZERO 10.56 9.27 3.58

01/08/2008 2:53:29 PM - ZERO 11.42 9.47 5.96

Page 23 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 2:53:59 PM - ZERO 11.58 9.53 6.04

01/08/2008 2:54:29 PM - ZERO 11.58 9.53 6.07

01/08/2008 2:54:59 PM - ZERO 11.56 9.55 6.24

01/08/2008 2:55:29 PM - ZERO 11.54 9.53 6.4

01/08/2008 2:55:59 PM RUN6 - 1 11.54 9.52 6.56

01/08/2008 2:56:29 PM RUN6 - 1 11.54 9.53 6.46

01/08/2008 2:56:59 PM RUN6 - 1 11.54 9.55 6.51

01/08/2008 2:57:29 PM RUN6 - 1 11.52 9.57 6.56

01/08/2008 2:57:59 PM RUN6 - 1 11.51 9.55 6.63

01/08/2008 2:58:29 PM RUN6 - 1 11.54 9.53 6.6

01/08/2008 2:58:59 PM RUN6 - 1 11.54 9.52 6.51

01/08/2008 2:59:29 PM RUN6 - 1 11.54 9.56 6.5

01/08/2008 2:59:59 PM RUN6 - 1 11.52 9.54 6.6

01/08/2008 3:00:29 PM RUN6 - 1 11.52 9.59 6.72

01/08/2008 3:00:59 PM RUN6 - 1 11.51 9.52 6.9

01/08/2008 3:01:29 PM RUN6 - 1 11.51 9.56 6.68

01/08/2008 3:01:59 PM RUN6 - 1 11.53 9.54 6.74

01/08/2008 3:02:29 PM RUN6 - 1 11.51 9.57 6.63

01/08/2008 3:02:59 PM RUN6 - 1 11.52 9.58 6.46

01/08/2008 3:03:29 PM RUN6 - 1 11.52 9.55 6.57

01/08/2008 3:03:59 PM RUN6 - 1 11.51 9.56 6.71

01/08/2008 3:04:29 PM RUN6 - 1 11.51 9.59 6.51

01/08/2008 3:04:59 PM RUN6 - 1 11.51 9.56 6.58

01/08/2008 3:05:29 PM RUN6 - 1 11.47 9.56 6.98

01/08/2008 3:05:59 PM RUN6 - 1 11.43 9.56 7.21

01/08/2008 3:06:29 PM RUN6 - 1 11.47 9.56 6.84

01/08/2008 3:06:59 PM RUN6 - 1 11.5 9.55 6.67

01/08/2008 3:07:29 PM RUN6 - 1 11.51 9.54 6.79

01/08/2008 3:07:59 PM RUN6 - 1 11.5 9.56 6.68

01/08/2008 3:08:29 PM RUN6 - 1 11.51 9.57 6.55

01/08/2008 3:08:59 PM RUN6 - 1 11.53 9.54 6.52

01/08/2008 3:09:29 PM RUN6 - 1 11.53 9.52 6.58

01/08/2008 3:09:59 PM RUN6 - 1 11.53 9.53 6.46

01/08/2008 3:10:29 PM RUN6 - 1 11.54 9.51 6.45

01/08/2008 3:10:59 PM RUN6 - 1 11.52 9.53 6.47

01/08/2008 3:11:29 PM RUN6 - 1 11.52 9.55 6.38

01/08/2008 3:11:59 PM RUN6 - 1 11.55 9.54 6.32

01/08/2008 3:12:29 PM RUN6 - 1 11.54 9.54 6.22

01/08/2008 3:12:59 PM RUN6 - 1 11.55 9.52 6.25

01/08/2008 3:13:29 PM RUN6 - 1 11.55 9.52 6.18

Page 24 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 3:13:59 PM RUN6 - 1 11.56 9.52 6.26

01/08/2008 3:14:29 PM RUN6 - 1 11.54 9.51 6.44

01/08/2008 3:14:59 PM RUN6 - 1 11.53 9.51 6.47

01/08/2008 3:15:29 PM RUN6 - 1 11.52 9.51 6.73

01/08/2008 3:15:59 PM RUN6 - 1 11.46 9.53 6.77

01/08/2008 3:16:29 PM RUN6 - 1 11.51 9.53 6.52

01/08/2008 3:16:59 PM 11.54 9.53 6.45

01/08/2008 3:17:29 PM 10.38 9.36 1.82

01/08/2008 3:17:59 PM 0.2 3.93 -0.09

01/08/2008 3:18:29 PM 0.05 3.72 -0.13

01/08/2008 3:18:59 PM 0.03 3.71 -0.11

01/08/2008 3:19:29 PM 0.03 3.7 -0.13

01/08/2008 3:19:59 PM - Span 0.03 3.69 -0.11

01/08/2008 3:20:29 PM - ZERO 0.03 3.69 -0.12

01/08/2008 3:20:59 PM - ZERO 0.03 3.69 -0.1

01/08/2008 3:21:29 PM - ZERO 0.04 3.68 3.61

01/08/2008 3:21:59 PM - ZERO 0.03 0.18 7.89

01/08/2008 3:22:29 PM - Span 0.04 0.02 7.96

01/08/2008 3:22:59 PM - Span 0.03 0.01 7.96

01/08/2008 3:23:29 PM - Span 2.93 1.45 3.33

01/08/2008 3:23:59 PM - Span 10.03 8.31 0.15

01/08/2008 3:24:29 PM - Span 10.5 9.2 0

01/08/2008 3:24:59 PM - ZERO 10.5 9.21 -0.01

01/08/2008 3:25:29 PM - ZERO 10.5 9.23 -0.02

01/08/2008 3:25:59 PM - ZERO 10.49 9.26 1.78

01/08/2008 3:26:29 PM - ZERO 11.26 9.49 1.82

01/08/2008 3:26:59 PM - ZERO 10.51 9.28 1.92

01/08/2008 3:27:29 PM - ZERO 10.97 9.47 5.49

01/08/2008 3:27:59 PM - ZERO 0.4 0.83 7.85

01/08/2008 3:28:29 PM - ZERO 0.06 0.06 7.96

01/08/2008 3:28:59 PM - ZERO 0.05 0.02 8.06

01/08/2008 3:29:29 PM - ZERO 0.04 0 7.97

01/08/2008 3:29:59 PM - ZERO 0.02 0 7.67

01/08/2008 3:30:29 PM - ZERO 6.98 5.25 2.12

01/08/2008 3:30:59 PM - ZERO 11.06 9.15 6.23

01/08/2008 3:31:29 PM - ZERO 11.44 9.49 5.91

01/08/2008 3:31:59 PM - ZERO 11.53 9.53 6.53

01/08/2008 3:32:29 PM - ZERO 11.54 9.54 6.46

01/08/2008 3:32:59 PM RUN7 - 1 11.53 9.53 6.52

01/08/2008 3:33:29 PM RUN7 - 1 11.54 9.53 6.53

Page 25 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 3:33:59 PM RUN7 - 1 11.52 9.54 6.67

01/08/2008 3:34:29 PM RUN7 - 1 11.52 9.54 6.64

01/08/2008 3:34:59 PM RUN7 - 1 11.52 9.55 6.77

01/08/2008 3:35:29 PM RUN7 - 1 11.51 9.55 6.87

01/08/2008 3:35:59 PM RUN7 - 1 11.49 9.57 6.69

01/08/2008 3:36:29 PM RUN7 - 1 11.5 9.55 6.72

01/08/2008 3:36:59 PM RUN7 - 1 11.52 9.55 6.68

01/08/2008 3:37:29 PM RUN7 - 1 11.52 9.55 6.66

01/08/2008 3:37:59 PM RUN7 - 1 11.52 9.55 6.54

01/08/2008 3:38:29 PM RUN7 - 1 11.52 9.56 6.53

01/08/2008 3:38:59 PM RUN7 - 1 11.51 9.54 6.55

01/08/2008 3:39:29 PM RUN7 - 1 11.51 9.51 6.74

01/08/2008 3:39:59 PM RUN7 - 1 11.54 9.52 6.69

01/08/2008 3:40:29 PM RUN7 - 1 11.5 9.54 6.83

01/08/2008 3:40:59 PM RUN7 - 1 11.49 9.51 7.1

01/08/2008 3:41:29 PM RUN7 - 1 11.48 9.54 7.04

01/08/2008 3:41:59 PM RUN7 - 1 11.47 9.53 7.1

01/08/2008 3:42:29 PM RUN7 - 1 11.49 9.54 6.96

01/08/2008 3:42:59 PM RUN7 - 1 11.49 9.52 7.09

01/08/2008 3:43:29 PM RUN7 - 1 11.49 9.53 7.01

01/08/2008 3:43:59 PM RUN7 - 1 11.48 9.52 6.95

01/08/2008 3:44:29 PM RUN7 - 1 11.5 9.52 6.77

01/08/2008 3:44:59 PM RUN7 - 1 11.5 9.53 6.74

01/08/2008 3:45:29 PM RUN7 - 1 11.49 9.55 7

01/08/2008 3:45:59 PM RUN7 - 1 11.43 9.57 7.24

01/08/2008 3:46:29 PM RUN7 - 1 11.46 9.59 6.81

01/08/2008 3:46:59 PM RUN7 - 1 11.52 9.57 6.45

01/08/2008 3:47:29 PM RUN7 - 1 11.52 9.57 6.52

01/08/2008 3:47:59 PM RUN7 - 1 11.54 9.57 6.48

01/08/2008 3:48:29 PM RUN7 - 1 11.53 9.55 6.54

01/08/2008 3:48:59 PM RUN7 - 1 11.52 9.58 6.7

01/08/2008 3:49:29 PM RUN7 - 1 11.52 9.55 6.67

01/08/2008 3:49:59 PM RUN7 - 1 11.52 9.59 6.41

01/08/2008 3:50:29 PM RUN7 - 1 11.53 9.56 6.54

01/08/2008 3:50:59 PM RUN7 - 1 11.51 9.53 6.74

01/08/2008 3:51:29 PM RUN7 - 1 11.51 9.54 6.69

01/08/2008 3:51:59 PM RUN7 - 1 11.53 9.55 6.58

01/08/2008 3:52:29 PM RUN7 - 1 11.55 9.54 6.51

01/08/2008 3:52:59 PM RUN7 - 1 11.55 9.54 6.41

01/08/2008 3:53:29 PM RUN7 - 1 11.55 9.52 6.51

Page 26 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 3:53:59 PM 11.52 9.54 6.48

01/08/2008 3:54:29 PM 11.55 9.53 5.96

01/08/2008 3:54:59 PM 1.06 4.28 0.41

01/08/2008 3:55:29 PM 0.05 3.69 -0.11

01/08/2008 3:55:59 PM 0.04 3.69 -0.12

01/08/2008 3:56:29 PM 0.04 3.68 -0.12

01/08/2008 3:56:59 PM 0.03 3.67 -0.12

01/08/2008 3:57:29 PM - ZERO 0.02 3.67 -0.13

01/08/2008 3:57:59 PM - ZERO 0.03 3.66 -0.11

01/08/2008 3:58:29 PM - ZERO 0.03 3.58 4.17

01/08/2008 3:58:59 PM - Span 0.04 0.08 7.91

01/08/2008 3:59:29 PM - Span 0.02 0.01 7.94

01/08/2008 3:59:59 PM - Span 0.03 0 7.95

01/08/2008 4:00:29 PM - ZERO 0.04 -0.01 7.95

01/08/2008 4:00:59 PM - ZERO 0.02 -0.01 7.55

01/08/2008 4:01:29 PM - ZERO 7.43 5.5 1.21

01/08/2008 4:01:59 PM - ZERO 10.44 9.05 -0.01

01/08/2008 4:02:29 PM - ZERO 10.5 9.19 -0.02

01/08/2008 4:02:59 PM - ZERO 10.49 9.22 -0.02

01/08/2008 4:03:59 PM 11.53 9.47 6.07

01/08/2008 4:04:29 PM 11.58 9.49 6.15

01/08/2008 4:04:59 PM 11.58 9.49 6.16

01/08/2008 4:05:29 PM 11.57 9.47 6.32

01/08/2008 4:05:59 PM 11.59 9.5 6.22

01/08/2008 4:06:29 PM 11.55 9.47 6.51

01/08/2008 4:06:59 PM 11.56 9.49 6.42

01/08/2008 4:07:29 PM 11.55 9.49 6.44

01/08/2008 4:07:59 PM RUN8 - 1 11.54 9.51 6.46

01/08/2008 4:08:29 PM RUN8 - 1 11.56 9.5 6.34

01/08/2008 4:08:59 PM RUN8 - 1 11.55 9.5 6.4

01/08/2008 4:09:29 PM RUN8 - 1 11.56 9.49 6.4

01/08/2008 4:09:59 PM RUN8 - 1 11.57 9.5 6.3

01/08/2008 4:10:29 PM RUN8 - 1 11.52 9.5 6.63

01/08/2008 4:10:59 PM RUN8 - 1 11.46 9.5 6.84

01/08/2008 4:11:29 PM RUN8 - 1 11.47 9.51 6.89

01/08/2008 4:11:59 PM RUN8 - 1 11.52 9.5 6.61

01/08/2008 4:12:29 PM RUN8 - 1 11.54 9.48 6.67

01/08/2008 4:12:59 PM RUN8 - 1 11.53 9.49 6.6

01/08/2008 4:13:29 PM RUN8 - 1 11.53 9.5 6.66

01/08/2008 4:13:59 PM RUN8 - 1 11.52 9.5 6.68

Page 27 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 4:14:29 PM RUN8 - 1 11.5 9.48 6.85

01/08/2008 4:14:59 PM RUN8 - 1 11.5 9.51 6.93

01/08/2008 4:15:29 PM RUN8 - 1 11.49 9.53 6.87

01/08/2008 4:15:59 PM RUN8 - 1 11.48 9.52 6.92

01/08/2008 4:16:29 PM RUN8 - 1 11.47 9.51 7.12

01/08/2008 4:16:59 PM RUN8 - 1 11.46 9.52 7.05

01/08/2008 4:17:29 PM RUN8 - 1 11.47 9.5 7.08

01/08/2008 4:17:59 PM RUN8 - 1 11.46 9.52 7.07

01/08/2008 4:18:29 PM RUN8 - 1 11.49 9.52 6.95

01/08/2008 4:18:59 PM RUN8 - 1 11.51 9.51 6.85

01/08/2008 4:19:29 PM RUN8 - 1 11.48 9.52 6.95

01/08/2008 4:19:59 PM RUN8 - 1 11.48 9.5 7.03

01/08/2008 4:20:29 PM RUN8 - 1 11.48 9.52 7.07

01/08/2008 4:20:59 PM RUN8 - 1 11.48 9.52 7.14

01/08/2008 4:21:29 PM RUN8 - 1 11.46 9.52 7.29

01/08/2008 4:21:59 PM RUN8 - 1 11.46 9.5 7.42

01/08/2008 4:22:29 PM RUN8 - 1 11.43 9.52 7.46

01/08/2008 4:22:59 PM RUN8 - 1 11.44 9.51 7.42

01/08/2008 4:23:29 PM RUN8 - 1 11.46 9.51 7.21

01/08/2008 4:23:59 PM RUN8 - 1 11.46 9.51 7.12

01/08/2008 4:24:29 PM RUN8 - 1 11.47 9.51 7.3

01/08/2008 4:24:59 PM RUN8 - 1 11.47 9.54 7.02

01/08/2008 4:25:29 PM RUN8 - 1 11.48 9.52 7.13

01/08/2008 4:25:59 PM RUN8 - 1 11.42 9.53 7.37

01/08/2008 4:26:29 PM RUN8 - 1 11.44 9.52 7.13

01/08/2008 4:26:59 PM RUN8 - 1 11.49 9.5 6.93

01/08/2008 4:27:29 PM RUN8 - 1 11.5 9.49 7.03

01/08/2008 4:27:59 PM RUN8 - 1 11.48 9.5 7.08

01/08/2008 4:28:29 PM RUN8 - 1 11.51 9.5 6.89

01/08/2008 4:28:59 PM 11.5 9.51 6.85

01/08/2008 4:29:29 PM 11.5 9.49 5.9

01/08/2008 4:29:59 PM 2.45 5.6 0.33

01/08/2008 4:30:29 PM 0.04 3.72 -0.12

01/08/2008 4:30:59 PM - Span 0.03 3.69 -0.1

01/08/2008 4:31:29 PM - ZERO 0.03 3.68 -0.1

01/08/2008 4:31:59 PM - ZERO 0.03 3.68 -0.12

01/08/2008 4:32:29 PM - ZERO 0.03 2.55 5.94

01/08/2008 4:32:59 PM - ZERO 0.03 0.04 7.96

01/08/2008 4:33:29 PM - Span 0.04 0.02 7.98

01/08/2008 4:33:59 PM - Span 0.03 0.01 7.96

Page 28 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 4:34:29 PM - Span 6.25 4.49 1.88

01/08/2008 4:34:59 PM - Span 10.39 8.92 0.05

01/08/2008 4:35:29 PM - ZERO 10.48 9.2 0.02

01/08/2008 4:35:59 PM - ZERO 10.48 9.22 0.01

01/08/2008 4:36:29 PM - ZERO 10.48 9.23 0.02

01/08/2008 4:36:59 PM - ZERO 11.07 9.33 4.13

01/08/2008 4:37:29 PM - ZERO 11.49 9.45 6.57

01/08/2008 4:37:59 PM - ZERO 11.5 9.49 6.7

01/08/2008 4:38:29 PM - ZERO 11.52 9.48 6.7

01/08/2008 4:38:59 PM - ZERO 11.49 9.48 6.79

01/08/2008 4:39:29 PM run9 - 1 11.5 9.5 6.78

01/08/2008 4:39:59 PM run9 - 1 11.51 9.48 6.74

01/08/2008 4:40:29 PM run9 - 1 11.49 9.48 6.86

01/08/2008 4:40:59 PM run9 - 1 11.49 9.5 6.92

01/08/2008 4:41:29 PM run9 - 1 11.48 9.47 7.01

01/08/2008 4:41:59 PM run9 - 1 11.49 9.49 6.91

01/08/2008 4:42:29 PM run9 - 1 11.52 9.49 6.69

01/08/2008 4:42:59 PM run9 - 1 11.51 9.48 6.91

01/08/2008 4:43:29 PM run9 - 1 11.5 9.52 6.79

01/08/2008 4:43:59 PM run9 - 1 11.51 9.5 6.81

01/08/2008 4:44:29 PM run9 - 1 11.49 9.49 6.96

01/08/2008 4:44:59 PM run9 - 1 11.52 9.49 6.92

01/08/2008 4:45:29 PM run9 - 1 11.53 9.5 6.82

01/08/2008 4:45:59 PM run9 - 1 11.52 9.49 6.89

01/08/2008 4:46:29 PM run9 - 1 11.51 9.49 6.87

01/08/2008 4:46:59 PM run9 - 1 11.52 9.49 6.89

01/08/2008 4:47:29 PM run9 - 1 11.53 9.49 6.61

01/08/2008 4:47:59 PM run9 - 1 11.53 9.49 6.72

01/08/2008 4:48:29 PM run9 - 1 11.52 9.49 6.83

01/08/2008 4:48:59 PM run9 - 1 11.52 9.49 6.72

01/08/2008 4:49:29 PM run9 - 1 11.53 9.49 6.81

01/08/2008 4:49:59 PM run9 - 1 11.51 9.49 6.95

01/08/2008 4:50:29 PM run9 - 1 11.51 9.47 6.99

01/08/2008 4:50:59 PM run9 - 1 11.45 9.49 7.44

01/08/2008 4:51:29 PM run9 - 1 11.43 9.51 7.37

01/08/2008 4:51:59 PM run9 - 1 11.51 9.48 6.88

01/08/2008 4:52:29 PM run9 - 1 11.51 9.5 6.81

01/08/2008 4:52:59 PM run9 - 1 11.51 9.47 6.72

01/08/2008 4:53:29 PM run9 - 1 11.53 9.49 6.71

01/08/2008 4:53:59 PM run9 - 1 11.54 9.49 6.68

Page 29 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 4:54:29 PM run9 - 1 11.54 9.47 6.63

01/08/2008 4:54:59 PM run9 - 1 11.55 9.48 6.72

01/08/2008 4:55:29 PM run9 - 1 11.53 9.51 6.58

01/08/2008 4:55:59 PM run9 - 1 11.53 9.47 6.69

01/08/2008 4:56:29 PM run9 - 1 11.52 9.47 6.76

01/08/2008 4:56:59 PM run9 - 1 11.51 9.49 6.86

01/08/2008 4:57:29 PM run9 - 1 11.51 9.48 6.8

01/08/2008 4:57:59 PM run9 - 1 11.54 9.46 6.59

01/08/2008 4:58:29 PM run9 - 1 11.54 9.48 6.69

01/08/2008 4:58:59 PM run9 - 1 11.53 9.48 6.64

01/08/2008 4:59:29 PM run9 - 1 11.55 9.46 6.56

01/08/2008 4:59:59 PM run9 - 1 11.55 9.47 6.74

01/08/2008 5:00:29 PM 11.53 9.49 6.77

01/08/2008 5:00:59 PM 11.53 9.51 6.01

01/08/2008 5:01:29 PM 2.83 5.85 0.4

01/08/2008 5:01:59 PM 0.06 3.73 -0.11

01/08/2008 5:02:29 PM 0.04 3.71 -0.13

01/08/2008 5:02:59 PM - ZERO 0.05 3.69 -0.1

01/08/2008 5:03:29 PM - ZERO 0.03 3.69 -0.11

01/08/2008 5:03:59 PM - ZERO 0.04 3.27 4.61

01/08/2008 5:04:29 PM - Span 0.03 0.07 7.94

01/08/2008 5:04:59 PM - ZERO 0.03 0.02 7.98

01/08/2008 5:05:29 PM - ZERO 0.04 0 7.8

01/08/2008 5:05:59 PM - ZERO 7.66 5.72 1.46

01/08/2008 5:06:29 PM - ZERO 10.46 9.08 0.04

01/08/2008 5:06:59 PM - Span 10.5 9.22 -0.01

01/08/2008 5:07:29 PM - ZERO 10.49 9.22 0.03

01/08/2008 5:07:59 PM - ZERO 10.49 9.24 -0.01

01/08/2008 5:08:29 PM - ZERO 17.48 4.74 0.12

01/08/2008 5:08:59 PM - ZERO 14.89 4.12 0.03

01/08/2008 5:09:29 PM - ZERO 20.27 1.31 0.18

01/08/2008 5:09:59 PM - ZERO 20.87 0.1 0.25

01/08/2008 5:10:29 PM - ZERO 20.87 0.07 0.22

01/08/2008 5:10:59 PM - ZERO 20.87 0.06 0.24

01/08/2008 5:11:29 PM - ZERO 20.88 0.06 0.25

01/08/2008 5:11:59 PM - ZERO 20.88 0.05 0.23

01/08/2008 5:12:29 PM - ZERO 20.89 0.03 0.23

01/08/2008 5:12:59 PM - ZERO 20.88 0.05 0.24

01/08/2008 5:13:29 PM - ZERO 20.9 0.02 0.24

01/08/2008 5:13:59 PM - ZERO 20.91 0.03 0.24

Page 30 of 31
LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM)cCO (PPM)

01/08/2008 5:14:29 PM - ZERO 20.91 0.02 0.27

01/08/2008 5:14:59 PM - ZERO 20.9 0.02 0.23

01/08/2008 5:15:29 PM - ZERO 20.88 0.02 0.27

01/08/2008 5:15:59 PM - ZERO 20.84 0.01 0.27

01/08/2008 5:16:29 PM - ZERO 20.8 0.01 0.29

01/08/2008 5:16:59 PM - ZERO 20.78 0 0.31

01/08/2008 5:17:29 PM - ZERO 20.76 0 0.28

01/08/2008 5:17:59 PM - ZERO 20.73 0.01 0.32

01/08/2008 5:18:29 PM - ZERO 20.75 0 0.33

01/08/2008 5:18:59 PM - ZERO 20.7 0.03 0.36

01/08/2008 5:19:29 PM - ZERO 20.71 0.04 0.33

Page 31 of 31
CYLINDER GAS CERTIFICATES 




APPENDIX B 

TURBINE DATA 
Plant Information Database Query Results

Plant Information Source: polk-1pisrv

Start Time: 01/08/2008 10:46

End Time: 01/08/2008 17:00

Time Interval: 1 Min

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 10:46:00 179.1152649 7131.787598 72.709274 1.29266

08-Jan-08 10:47:00 178.9632568 7064.672852 72.632591 1.29276

08-Jan-08 10:48:00 178.2445831 7062.369141 72.555908 1.29287

08-Jan-08 10:49:00 178.1081543 7099.312012 72.574768 1.29297

08-Jan-08 10:50:00 178.7349701 7150.769531 72.880249 1.29307

08-Jan-08 10:51:00 179.2855682 7111.020508 73.062531 1.29317

08-Jan-08 10:52:00 179.4393463 7082.110352 72.751999 1.29327

08-Jan-08 10:53:00 177.88797 7049.321289 72.862427 1.29338

08-Jan-08 10:54:00 178.4517975 7064.905273 73.167915 1.29348

08-Jan-08 10:55:00 180.3786163 7102.365723 73.3647 1.29358

08-Jan-08 10:56:00 179.5168152 7098.838379 73.136871 1.29368

08-Jan-08 10:57:00 180.119751 7085.383301 73.25927 1.29378

08-Jan-08 10:58:00 180.419632 7064.538574 73.38166 1.29389

08-Jan-08 10:59:00 178.8349457 7062.338379 73.504051 1.29399

08-Jan-08 11:00:00 178.8848877 7086.172852 73.626442 1.29409

08-Jan-08 11:01:00 178.3968201 7076.088867 73.74884 1.29419

08-Jan-08 11:02:00 178.3382721 7052.737305 74.35659 1.29429

08-Jan-08 11:03:00 178.1646118 7036.25293 74.451248 1.2944

08-Jan-08 11:04:00 178.0582123 7076.700195 74.527931 1.2945

08-Jan-08 11:05:00 179.8825073 7172.990234 74.604614 1.2946

08-Jan-08 11:06:00 178.8912659 7074.121094 74.68129 1.2947

08-Jan-08 11:07:00 178.7831573 7061.745605 74.418182 1.2948

08-Jan-08 11:08:00 178.5129852 7080.812988 74.644043 1.29491

08-Jan-08 11:09:00 178.2707214 7085.194824 74.426285 1.29501

08-Jan-08 11:10:00 179.6755829 7120.695313 74.115753 1.29511

08-Jan-08 11:11:00 179.5765228 7117.541992 74.501862 1.29521

08-Jan-08 11:12:00 178.4888153 7104.060547 74.654602 1.29531

08-Jan-08 11:13:00 178.8935242 7124.995605 74.611099 1.29541

08-Jan-08 11:14:00 178.455246 8221.917969 74.507874 1.29552

08-Jan-08 11:15:00 178.3178253 7182.096191 74.404648 1.29562

08-Jan-08 11:16:00 179.2839966 7127.008301 74.288399 1.29572

08-Jan-08 11:17:00 179.3051605 7100.53418 74.761711 1.29582

08-Jan-08 11:18:00 178.3685608 7085.14502 74.863815 1.29592

08-Jan-08 11:19:00 177.9571991 7062.219727 74.965919 1.29603

08-Jan-08 11:20:00 179.1837463 7103.149902 74.8853 1.29613

08-Jan-08 11:21:00 179.1481628 7110.525391 75.193283 1.29623

08-Jan-08 11:22:00 179.6767883 7112.268066 75.091339 1.29633

08-Jan-08 11:23:00 178.7565002 7090.670898 75.246605 1.29643

08-Jan-08 11:24:00 179.3795624 7115.965332 75.541046 1.29654

08-Jan-08 11:25:00 179.4131012 7107.128418 75.391335 1.29664

Page 1 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 11:26:00 178.4233856 7056.306641 75.463776 1.29674

08-Jan-08 11:27:00 179.1598206 7109.922852 75.481163 1.29684

08-Jan-08 11:28:00 178.674881 7087.876465 75.407585 1.29694

08-Jan-08 11:29:00 177.7310181 7132.044434 75.610062 1.29705

08-Jan-08 11:30:00 179.1592712 7250.276367 75.812538 1.29715

08-Jan-08 11:31:00 179.3124237 7148.350586 75.691055 1.29725

08-Jan-08 11:32:00 179.3832245 7117.108398 75.051193 1.29735

08-Jan-08 11:33:00 179.5561218 7133.242188 75.181664 1.29745

08-Jan-08 11:34:00 178.7237091 7111.986816 75.312126 1.29755

08-Jan-08 11:35:00 178.5356445 7110.654297 75.442596 1.29766

08-Jan-08 11:36:00 177.553894 7096.928223 75.573059 1.29776

08-Jan-08 11:37:00 178.2543793 7070.222168 75.703529 1.29786

08-Jan-08 11:38:00 177.7529297 7091.648438 75.834 1.29796

08-Jan-08 11:39:00 178.598053 7087.125977 75.863312 1.29806

08-Jan-08 11:40:00 179.4431763 7111.779297 75.682495 1.29817

08-Jan-08 11:41:00 179.3820038 7092.186035 75.877884 1.29827

08-Jan-08 11:42:00 178.3091278 7073.497559 75.571663 1.29837

08-Jan-08 11:43:00 179.0954895 7067.630859 74.980064 1.29847

08-Jan-08 11:44:00 179.298111 7125.781738 74.824799 1.29857

08-Jan-08 11:45:00 178.4942322 7205.20752 74.417679 1.29868

08-Jan-08 11:46:00 179.5084229 7140.42041 74.823257 1.29878

08-Jan-08 11:47:00 179.091156 7142.470215 75.228836 1.29888

08-Jan-08 11:48:00 179.9411011 7153.193359 75.615906 1.29898

08-Jan-08 11:49:00 179.3661346 7132.973145 75.466187 1.29908

08-Jan-08 11:50:00 178.407959 7119.45459 75.316475 1.29919

08-Jan-08 11:51:00 178.2354431 7120.187988 75.517845 1.29929

08-Jan-08 11:52:00 177.7017365 7095.840332 75.719223 1.29939

08-Jan-08 11:53:00 178.0559692 7095.058105 75.920593 1.29949

08-Jan-08 11:54:00 179.4611053 7125.927246 75.651199 1.29959

08-Jan-08 11:55:00 179.1287689 7195.424316 75.898087 1.2997

08-Jan-08 11:56:00 179.6149445 7133.376465 76.206078 1.2998

08-Jan-08 11:57:00 180.3777161 7125.120117 76.069191 1.2999

08-Jan-08 11:58:00 180.0175018 7124.411133 75.863861 1.3

08-Jan-08 11:59:00 179.6572723 7115.525391 75.658539 1.3001

08-Jan-08 12:00:00 179.5390015 7122.418945 75.620895 1.3002

08-Jan-08 12:01:00 178.1641693 7123.943848 75.620895 1.30031

08-Jan-08 12:02:00 177.8606873 7135.967773 75.316475 1.30041

08-Jan-08 12:03:00 179.5675201 7138.88916 75.749657 1.30051

08-Jan-08 12:04:00 180.4973297 7153.019531 75.92524 1.30061

08-Jan-08 12:05:00 180.4523163 7144.951172 76.100815 1.30071

08-Jan-08 12:06:00 179.7201843 7123.94043 76.276398 1.30082

08-Jan-08 12:07:00 179.115097 7112.94043 76.451981 1.30092

08-Jan-08 12:08:00 178.3156433 7099.373047 76.627563 1.30102

08-Jan-08 12:09:00 178.1337891 7122.26123 76.803139 1.30112

08-Jan-08 12:10:00 179.4345398 7229.396973 77.186501 1.30122

Page 2 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 12:11:00 179.7134247 7107.587402 77.186501 1.30133

08-Jan-08 12:12:00 179.1413879 7094.539063 76.790565 1.30143

08-Jan-08 12:13:00 179.1005249 7023.944336 76.6353 1.30153

08-Jan-08 12:14:00 179.2047424 7102.599609 76.821762 1.30163

08-Jan-08 12:15:00 178.6329193 7112.316895 76.718536 1.30173

08-Jan-08 12:16:00 179.3988495 7112.90332 76.615311 1.30184

08-Jan-08 12:17:00 180.2948608 7084.375977 76.647522 1.30194

08-Jan-08 12:18:00 179.6038513 7093.835938 77.143959 1.30204

08-Jan-08 12:19:00 178.6726837 7126.287109 77.041847 1.30214

08-Jan-08 12:20:00 178.6734314 7116.937012 76.939743 1.30224

08-Jan-08 12:21:00 178.4564209 7113.343262 76.763786 1.30235

08-Jan-08 12:22:00 177.7546997 7107.989746 76.873375 1.30245

08-Jan-08 12:23:00 178.4224701 7099.754395 76.873375 1.30255

08-Jan-08 12:24:00 179.0210419 7160.565918 77.125237 1.30265

08-Jan-08 12:25:00 178.9950256 7225.507324 76.921028 1.30275

08-Jan-08 12:26:00 178.8213806 7092.57666 76.71682 1.30285

08-Jan-08 12:27:00 177.9845581 7112.191895 76.701668 1.30296

08-Jan-08 12:28:00 178.4194489 7135.109375 76.998627 1.30306

08-Jan-08 12:29:00 178.2599182 7129.361328 76.588486 1.30316

08-Jan-08 12:30:00 178.5670166 7162.430176 76.742485 1.30326

08-Jan-08 12:31:00 178.8016052 7122.247559 76.850082 1.30336

08-Jan-08 12:32:00 179.3899689 7187.681641 76.694817 1.30347

08-Jan-08 12:33:00 179.4660645 7145.904785 76.873375 1.30357

08-Jan-08 12:34:00 179.561142 7163 76.570412 1.30367

08-Jan-08 12:35:00 179.5748749 7191.409668 76.671967 1.30377

08-Jan-08 12:36:00 179.1436615 7105.338867 76.773514 1.30387

08-Jan-08 12:37:00 177.9611359 7069.89209 76.865677 1.30398

08-Jan-08 12:38:00 177.9658966 7106.193359 76.403702 1.30408

08-Jan-08 12:39:00 178.9095154 7082.579102 75.941719 1.30418

08-Jan-08 12:40:00 178.1005249 7116.460449 76.335632 1.30428

08-Jan-08 12:41:00 179.4108276 7097.209473 76.744049 1.30438

08-Jan-08 12:42:00 179.5126495 7104.848633 77.152466 1.30449

08-Jan-08 12:43:00 179.450119 7119.271484 76.339539 1.30459

08-Jan-08 12:44:00 179.4321136 7133.694336 76.384605 1.30469

08-Jan-08 12:45:00 179.8762512 7123.079102 76.537346 1.30479

08-Jan-08 12:46:00 178.3610992 7108.044922 77.092567 1.30489

08-Jan-08 12:47:00 178.1867676 7093.634766 77.002769 1.305

08-Jan-08 12:48:00 178.7910309 7079.333984 77.158035 1.3051

08-Jan-08 12:49:00 178.4533234 7096.512695 76.998627 1.3052

08-Jan-08 12:50:00 178.1156158 7176.925781 77.066849 1.3053

08-Jan-08 12:51:00 178.8391418 7087.211914 76.914108 1.3054

08-Jan-08 12:52:00 179.2713928 7079.083496 76.761368 1.3055

08-Jan-08 12:53:00 179.4935303 7087.333984 76.608627 1.30561

08-Jan-08 12:54:00 179.7006531 7118.929688 76.770714 1.30571

08-Jan-08 12:55:00 179.6530304 7127.424316 76.668053 1.30581

Page 3 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 12:56:00 179.5771027 7134.146484 76.483261 1.30591

08-Jan-08 12:57:00 179.6116486 7084.308594 76.342888 1.30601

08-Jan-08 12:58:00 178.1365814 7078.625 76.498154 1.30612

08-Jan-08 12:59:00 178.4359894 7079.327637 76.247139 1.30622

08-Jan-08 13:00:00 178.4160309 7110.251465 76.247139 1.30632

08-Jan-08 13:01:00 179.38591 7132.618652 76.247139 1.30642

08-Jan-08 13:02:00 179.9172363 7132.924316 76.247139 1.30652

08-Jan-08 13:03:00 179.6038513 7081.078125 76.336967 1.30663

08-Jan-08 13:04:00 178.657486 7123.135742 75.874985 1.30673

08-Jan-08 13:05:00 178.5965881 7145.757813 75.759491 1.30683

08-Jan-08 13:06:00 178.3741302 7114.957031 76.067482 1.30693

08-Jan-08 13:07:00 178.7499695 7088.574219 75.990479 1.30703

08-Jan-08 13:08:00 179.2937469 7092.149414 75.98452 1.30714

08-Jan-08 13:09:00 178.9767609 7123.390625 76.560257 1.30724

08-Jan-08 13:10:00 179.3478088 7142.641602 76.560257 1.30734

08-Jan-08 13:11:00 179.2598419 7116.998047 76.560257 1.30744

08-Jan-08 13:12:00 178.9866638 7096.305176 76.375465 1.30754

08-Jan-08 13:13:00 178.713501 7095.697266 75.934021 1.30764

08-Jan-08 13:14:00 178.9220886 7126.094727 76.057213 1.30775

08-Jan-08 13:15:00 179.6804657 7219.578613 76.519196 1.30785

08-Jan-08 13:16:00 179.6472168 7147.078125 76.801514 1.30795

08-Jan-08 13:17:00 179.0704193 7099.776367 76.658737 1.30805

08-Jan-08 13:18:00 178.3297272 7062.057129 77.113266 1.30815

08-Jan-08 13:19:00 178.8196259 7068.290527 77.476517 1.30826

08-Jan-08 13:20:00 179.2898254 7115.788086 77.322525 1.30836

08-Jan-08 13:21:00 180.3114471 7139.94043 77.222435 1.30846

08-Jan-08 13:22:00 180.2920685 7136.175293 77.468819 1.30856

08-Jan-08 13:23:00 178.925293 7094.300781 77.160828 1.30866

08-Jan-08 13:24:00 177.4853973 7081.467285 76.580788 1.30877

08-Jan-08 13:25:00 177.7691193 7077.922363 76.99144 1.30887

08-Jan-08 13:26:00 178.0528412 7097.233887 77.402084 1.30897

08-Jan-08 13:27:00 178.2264557 7109.151367 77.812737 1.30907

08-Jan-08 13:28:00 179.495636 7117.792969 77.710632 1.30917

08-Jan-08 13:29:00 179.2988892 7144.422852 77.608528 1.30928

08-Jan-08 13:30:00 179.0223846 7208.485352 77.506424 1.30938

08-Jan-08 13:31:00 178.7661285 7127.482422 77.216805 1.30948

08-Jan-08 13:32:00 178.9600983 7109.733887 77.352272 1.30958

08-Jan-08 13:33:00 178.7225037 7092.687012 77.536461 1.30968

08-Jan-08 13:34:00 178.0629883 7088.268555 77.72065 1.30979

08-Jan-08 13:35:00 178.8065643 7133.227539 77.904839 1.30989

08-Jan-08 13:36:00 179.0046844 7132.681641 78.089027 1.30999

08-Jan-08 13:37:00 179.1823883 7130.027344 77.63308 1.31009

08-Jan-08 13:38:00 178.1557617 6892.980469 77.499619 1.31019

08-Jan-08 13:39:00 179.5645294 7126.834473 77.812737 1.31029

08-Jan-08 13:40:00 179.3068085 7134.351563 78.221153 1.3104

Page 4 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 13:41:00 178.9916229 7140.251465 78.62957 1.3105

08-Jan-08 13:42:00 178.3234253 7118.624023 78.752098 1.3106

08-Jan-08 13:43:00 178.7367096 7062.503418 78.752098 1.3107

08-Jan-08 13:44:00 179.6955566 7134.51123 78.654572 1.3108

08-Jan-08 13:45:00 179.1885071 7227.57666 78.43898 1.31091

08-Jan-08 13:46:00 179.115509 7187.464355 78.43898 1.31101

08-Jan-08 13:47:00 178.4027405 7132.050293 78.125862 1.31111

08-Jan-08 13:48:00 177.7938232 7121.704102 78.485184 1.31121

08-Jan-08 13:49:00 178.6226959 7113.786133 79.101151 1.31131

08-Jan-08 13:50:00 179.5726166 7135.602051 79.378342 1.31142

08-Jan-08 13:51:00 178.6563263 7142.286621 79.05249 1.31152

08-Jan-08 13:52:00 178.6054382 7126.274902 78.441528 1.31162

08-Jan-08 13:53:00 179.1507721 7110.263184 78.43898 1.31172

08-Jan-08 13:54:00 178.9419403 7133.620117 78.6828 1.31182

08-Jan-08 13:55:00 180.0388184 7248.005859 78.528809 1.31193

08-Jan-08 13:56:00 179.8782349 7156.575195 78.567307 1.31203

08-Jan-08 13:57:00 179.0166931 7091.686523 79.045593 1.31213

08-Jan-08 13:58:00 177.9540405 7088.049805 78.9944 1.31223

08-Jan-08 13:59:00 178.1096954 7090.120605 78.943214 1.31233

08-Jan-08 14:00:00 178.6350098 7109.823242 78.892021 1.31244

08-Jan-08 14:01:00 178.8851471 7122.222168 78.840828 1.31254

08-Jan-08 14:02:00 179.1624298 7130.229004 78.789635 1.31264

08-Jan-08 14:03:00 179.8405457 7143.438965 78.587837 1.31274

08-Jan-08 14:04:00 179.5478668 7129.321777 77.669014 1.31284

08-Jan-08 14:05:00 179.2276306 7129.672363 77.319962 1.31294

08-Jan-08 14:06:00 179.4122467 7133.217773 77.935936 1.31305

08-Jan-08 14:07:00 178.763031 7111.779297 78.551903 1.31315

08-Jan-08 14:08:00 177.789093 7089.436035 78.775391 1.31325

08-Jan-08 14:09:00 178.142334 7122.657227 78.930656 1.31335

08-Jan-08 14:10:00 178.3154755 7240.23291 78.769989 1.31345

08-Jan-08 14:11:00 178.5799713 7146.852051 78.923355 1.31356

08-Jan-08 14:12:00 179.0852051 7137.76416 79.076721 1.31366

08-Jan-08 14:13:00 179.7300568 7155.744141 79.230087 1.31376

08-Jan-08 14:14:00 179.6673431 7157.256836 79.373253 1.31386

08-Jan-08 14:15:00 180.0613251 7165.873535 79.220505 1.31396

08-Jan-08 14:16:00 178.7208099 7097.883789 79.067764 1.31407

08-Jan-08 14:17:00 178.4838715 7121.39209 79.216644 1.31417

08-Jan-08 14:18:00 179.3505707 7121.979004 79.370644 1.31427

08-Jan-08 14:19:00 179.2743988 7159.54541 78.939461 1.31437

08-Jan-08 14:20:00 179.2293701 7175.11084 78.477478 1.31447

08-Jan-08 14:21:00 179.2577667 7095.210449 78.721298 1.31458

08-Jan-08 14:22:00 179.6072845 7153.911621 78.301826 1.31468

08-Jan-08 14:23:00 178.3285217 7066.041504 78.146561 1.31478

08-Jan-08 14:24:00 178.365448 7094.227051 77.90667 1.31488

08-Jan-08 14:25:00 179.3854675 7285.911133 77.871292 1.31498

Page 5 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 14:26:00 178.6470184 7160.725098 77.565804 1.31509

08-Jan-08 14:27:00 177.9085693 7144.88623 77.744896 1.31519

08-Jan-08 14:28:00 179.9528046 7164.197754 77.735741 1.31529

08-Jan-08 14:29:00 177.9742889 7183.509766 77.696289 1.31539

08-Jan-08 14:30:00 179.4810333 7160.15625 77.541023 1.31549

08-Jan-08 14:31:00 180.138031 7156.51416 77.593811 1.31559

08-Jan-08 14:32:00 179.9744263 7237.523438 77.28833 1.3157

08-Jan-08 14:33:00 178.7901917 7145.024902 77.322639 1.3158

08-Jan-08 14:34:00 179.4471436 7157.181152 77.526848 1.3159

08-Jan-08 14:35:00 179.384903 7282.027832 77.731056 1.316

08-Jan-08 14:36:00 179.2475586 7189.545898 77.719574 1.3161

08-Jan-08 14:37:00 179.1102295 7145.910645 77.564316 1.31621

08-Jan-08 14:38:00 178.3059082 7132.068359 77.186501 1.31631

08-Jan-08 14:39:00 179.3768158 7140.227051 77.499619 1.31641

08-Jan-08 14:40:00 179.2567291 7126.599121 77.817871 1.31651

08-Jan-08 14:41:00 178.7969666 7127.414063 78.033463 1.31661

08-Jan-08 14:42:00 178.9230347 7137.069824 77.848671 1.31672

08-Jan-08 14:43:00 179.6874847 7146.725586 77.663879 1.31682

08-Jan-08 14:44:00 179.1483154 7141.816406 77.479088 1.31692

08-Jan-08 14:45:00 178.0257874 7127.057617 77.294296 1.31702

08-Jan-08 14:46:00 178.5913391 7121.196777 77.443153 1.31712

08-Jan-08 14:47:00 179.2274017 7122.452148 77.812737 1.31723

08-Jan-08 14:48:00 179.0940704 7131.243652 77.499619 1.31733

08-Jan-08 14:49:00 179.7062683 7163.019531 77.499619 1.31743

08-Jan-08 14:50:00 179.7756958 7279.377441 77.287506 1.31753

08-Jan-08 14:51:00 179.568573 7195.233887 76.905884 1.31763

08-Jan-08 14:52:00 178.7895966 7121.3125 77.008553 1.31773

08-Jan-08 14:53:00 178.4000092 7086.710449 77.111214 1.31784

08-Jan-08 14:54:00 178.6108093 7126.19043 77.019501 1.31794

08-Jan-08 14:55:00 179.1918488 7141.040039 76.64106 1.31804

08-Jan-08 14:56:00 178.9859161 7152.773926 76.801514 1.31814

08-Jan-08 14:57:00 178.7882538 7134.109863 76.49353 1.31824

08-Jan-08 14:58:00 178.5991364 7110.092285 76.309761 1.31835

08-Jan-08 14:59:00 178.4100342 7130.724121 76.529205 1.31845

08-Jan-08 15:00:00 178.0467987 7096.57373 76.37394 1.31855

08-Jan-08 15:01:00 178.8302765 7108.552246 76.322838 1.31865

08-Jan-08 15:02:00 179.4929962 7188.587402 76.735741 1.31875

08-Jan-08 15:03:00 179.8502808 7189.879883 77.148651 1.31886

08-Jan-08 15:04:00 179.8636475 7203.930664 77.590523 1.31896

08-Jan-08 15:05:00 178.8659363 7276.013672 78.089928 1.31906

08-Jan-08 15:06:00 178.7728577 7180.467285 77.828262 1.31916

08-Jan-08 15:07:00 178.2908783 7149.36377 77.983528 1.31926

08-Jan-08 15:08:00 178.6470032 7155.499512 78.138794 1.31937

08-Jan-08 15:09:00 178.4542694 7132.386719 78.294067 1.31947

08-Jan-08 15:10:00 179.5256958 7166.230957 78.129967 1.31957

Page 6 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 15:11:00 179.7207794 7205.257813 78.253166 1.31967

08-Jan-08 15:12:00 179.2569885 7203.705566 78.376358 1.31977

08-Jan-08 15:13:00 179.2663422 7143.266113 78.49955 1.31988

08-Jan-08 15:14:00 177.9451141 7135.356934 78.622742 1.31998

08-Jan-08 15:15:00 178.4899139 7232.729492 78.745941 1.32008

08-Jan-08 15:16:00 179.0346985 7164.572754 78.519554 1.32018

08-Jan-08 15:17:00 179.7854614 7148.159668 78.274765 1.32028

08-Jan-08 15:18:00 177.9840698 7102.966309 78.029984 1.32038

08-Jan-08 15:19:00 178.2372589 7098.603027 77.785202 1.32049

08-Jan-08 15:20:00 178.5299377 7108.870117 77.540413 1.32059

08-Jan-08 15:21:00 179.3815613 7121.135254 77.499619 1.32069

08-Jan-08 15:22:00 179.8530884 7165.668945 77.557022 1.32079

08-Jan-08 15:23:00 178.1047363 7104.634766 77.562241 1.32089

08-Jan-08 15:24:00 178.4437103 7100.32666 77.266479 1.321

08-Jan-08 15:25:00 179.9899292 7170.344238 77.368584 1.3211

08-Jan-08 15:26:00 179.2054443 7155.121582 77.470688 1.3212

08-Jan-08 15:27:00 178.56987 7169.017578 76.837448 1.3213

08-Jan-08 15:28:00 179.0098267 7173.784668 76.506577 1.3214

08-Jan-08 15:29:00 179.9178467 7182.536133 76.429901 1.32151

08-Jan-08 15:30:00 179.9994965 7257.094238 76.353218 1.32161

08-Jan-08 15:31:00 178.7411346 7188.222168 76.276535 1.32171

08-Jan-08 15:32:00 178.9490509 7152.499023 76.532028 1.32181

08-Jan-08 15:33:00 178.6989899 7140.154297 76.994011 1.32191

08-Jan-08 15:34:00 178.1134491 7127.809082 77.050812 1.32202

08-Jan-08 15:35:00 178.4286346 7166.164063 76.788681 1.32212

08-Jan-08 15:36:00 178.9046021 7173.570801 76.634689 1.32222

08-Jan-08 15:37:00 179.1338806 7157.574707 76.718094 1.32232

08-Jan-08 15:38:00 178.8821106 7138.69043 77.023575 1.32242

08-Jan-08 15:39:00 178.130249 7138.974609 76.899048 1.32253

08-Jan-08 15:40:00 177.2048035 7095.889648 76.514313 1.32263

08-Jan-08 15:41:00 177.2519226 7074.164063 76.412209 1.32273

08-Jan-08 15:42:00 177.833313 7147.530273 76.310104 1.32283

08-Jan-08 15:43:00 177.8109894 7090.802246 76.364563 1.32293

08-Jan-08 15:44:00 178.1754303 7125.453125 76.670876 1.32303

08-Jan-08 15:45:00 179.5802765 7225.565918 76.977188 1.32314

08-Jan-08 15:46:00 179.9667358 7217.967285 77.088966 1.32324

08-Jan-08 15:47:00 179.9586487 7186.010742 76.967316 1.32334

08-Jan-08 15:48:00 179.3937225 7154.054688 76.873375 1.32344

08-Jan-08 15:49:00 178.99823 7127.36377 77.186501 1.32354

08-Jan-08 15:50:00 179.0923309 7127 77.186501 1.32365

08-Jan-08 15:51:00 178.146759 7118.935547 77.186501 1.32375

08-Jan-08 15:52:00 177.437973 7071.743652 77.186501 1.32385

08-Jan-08 15:53:00 176.8746033 7056.490234 77.480896 1.32395

08-Jan-08 15:54:00 177.934845 7084.815918 77.378792 1.32405

08-Jan-08 15:55:00 177.0437469 7205.710449 77.276688 1.32416

Page 7 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 15:56:00 177.4345703 7103.956543 77.174583 1.32426

08-Jan-08 15:57:00 177.0386353 7041.132324 77.072479 1.32436

08-Jan-08 15:58:00 178.0343781 7040.350098 76.970375 1.32446

08-Jan-08 15:59:00 178.0695496 7067.949707 76.88903 1.32456

08-Jan-08 16:00:00 178.5622711 7083.074219 77.176292 1.32467

08-Jan-08 16:01:00 178.7369232 7096.253418 76.972076 1.32477

08-Jan-08 16:02:00 178.4115295 7111.598145 76.767868 1.32487

08-Jan-08 16:03:00 178.9309082 7106.547852 76.56366 1.32497

08-Jan-08 16:04:00 179.0524902 7094.080566 76.661209 1.32507

08-Jan-08 16:05:00 179.1412659 7098.554199 76.76387 1.32518

08-Jan-08 16:06:00 177.2951508 7070.466309 76.866531 1.32528

08-Jan-08 16:07:00 177.5951691 7101.169922 77.473526 1.32538

08-Jan-08 16:08:00 178.3530731 7106.205566 77.186501 1.32548

08-Jan-08 16:09:00 179.1670685 7105.716797 76.736221 1.32558

08-Jan-08 16:10:00 178.4266205 7235.036621 76.580956 1.32568

08-Jan-08 16:11:00 178.4643097 7138.149414 76.873375 1.32579

08-Jan-08 16:12:00 177.0715027 7092.974609 76.873375 1.32589

08-Jan-08 16:13:00 176.9838562 7089.776367 76.873375 1.32599

08-Jan-08 16:14:00 177.4191132 7104.628906 76.873375 1.32609

08-Jan-08 16:15:00 179.0372467 7181.978027 76.873375 1.32619

08-Jan-08 16:16:00 179.1507111 7174.921387 76.329269 1.3263

08-Jan-08 16:17:00 178.6657715 7160.987305 76.614151 1.3264

08-Jan-08 16:18:00 179.3302307 7164.393555 76.691147 1.3265

08-Jan-08 16:19:00 178.0054932 7169.038086 76.76815 1.3266

08-Jan-08 16:20:00 177.5633392 7173.682617 76.845146 1.3267

08-Jan-08 16:21:00 176.7914429 7133.968262 76.483261 1.32681

08-Jan-08 16:22:00 176.8251648 7179.199219 76.437065 1.32691

08-Jan-08 16:23:00 177.1393433 7146.509766 76.69072 1.32701

08-Jan-08 16:24:00 177.753067 7141.522949 76.81488 1.32711

08-Jan-08 16:25:00 177.0758667 7278.257324 76.711655 1.32721

08-Jan-08 16:26:00 176.274292 7147.678711 76.608429 1.32732

08-Jan-08 16:27:00 176.6844788 7065.577637 76.353226 1.32742

08-Jan-08 16:28:00 177.5896149 7079.87793 76.558548 1.32752

08-Jan-08 16:29:00 176.9016113 7067.655273 76.76387 1.32762

08-Jan-08 16:30:00 176.5413971 7057.388184 76.728462 1.32772

08-Jan-08 16:31:00 176.9637756 7072.177734 76.417931 1.32782

08-Jan-08 16:32:00 177.421524 7116.875 76.49556 1.32793

08-Jan-08 16:33:00 176.526825 7039.989258 76.340302 1.32803

08-Jan-08 16:34:00 176.484726 7053.075684 76.53672 1.32813

08-Jan-08 16:35:00 177.3074493 7163.32959 76.475327 1.32823

08-Jan-08 16:36:00 177.0774841 7112.060059 76.413933 1.32833

08-Jan-08 16:37:00 177.5226746 7097.436035 76.352531 1.32844

08-Jan-08 16:38:00 177.4752045 7078.484375 76.291138 1.32854

08-Jan-08 16:39:00 177.2970886 7074.495605 76.334404 1.32864

08-Jan-08 16:40:00 176.4541931 7083.15332 76.642387 1.32874

Page 8 of 9
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Average: 178.6 7124.9 76.7 1.3

08-Jan-08 16:41:00 176.876236 7093.42041 76.822601 1.32884

08-Jan-08 16:42:00 177.5938263 7064.281738 76.619499 1.32895

08-Jan-08 16:43:00 176.8300171 7078.337891 76.416389 1.32905

08-Jan-08 16:44:00 176.2491608 7030.693848 76.299324 1.32915

08-Jan-08 16:45:00 175.8907471 7037.020508 76.535004 1.32925

08-Jan-08 16:46:00 176.3048401 7053.290039 76.383499 1.32935

08-Jan-08 16:47:00 175.7822571 7098.26709 76.262604 1.32946

08-Jan-08 16:48:00 176.0436401 7027.65332 76.417229 1.32956

08-Jan-08 16:49:00 176.2176514 7063.038086 76.571854 1.32966

08-Jan-08 16:50:00 175.6544037 7092.240723 76.726479 1.32976

08-Jan-08 16:51:00 175.6316986 7072.364258 76.565392 1.32986

08-Jan-08 16:52:00 174.9238586 6997.057129 76.719383 1.32997

08-Jan-08 16:53:00 175.4199066 7027.973145 76.873375 1.33007

08-Jan-08 16:54:00 176.8538818 7044.82959 76.570358 1.33017

08-Jan-08 16:55:00 176.7458038 7062.827148 76.707909 1.33027

08-Jan-08 16:56:00 175.3784332 7050.512695 76.860649 1.33037

08-Jan-08 16:57:00 175.3651581 7037.770508 76.767723 1.33047

08-Jan-08 16:58:00 176.3011017 7071.046875 76.652466 1.33058

08-Jan-08 16:59:00 175.7945099 7025.039063 76.537209 1.33068

08-Jan-08 17:00:00 176.3952026 7077.909668 76.421944 1.33078

Page 9 of 9
APPENDIX C 

FUEL ANALYSIS 
Coal Derived Gas Heating Value Calculations

Customer: Tampa Electric Company Sample ID: PPS -001

Facility: Polk Power Station Analysis Date: 01/08/2008

Source: Unit 1

CALCULATION OF DENSITY AND HEATING VALUE @ 68°F and 29.92 in Hg

% volume Component Gross Volume

% Molecular Density x Gross Weight Heating Value Fract.

Component Volume Wt. (lb/ft3

) Density weight % Btu/lb Fract. Btu (Btu/SCF) Btu

Hydrogen 33.4600 2.016 0.00524 0.00175 3.0318 61000.2 1849.42 319.5 106.915

Oxygen 0.0000 31.999 0.08314 0.00000 0.0000 0 0.00 0.0 0

Argon 0.7000 39.948 0.10380 0.00073 1.2568 0 0.00 0.0 0

Nitrogen 3.2800 28.014 0.07279 0.00239 4.1299 0 0.00 0.0 0

CO2 18.1100 44.010 0.11435 0.02071 35.8227 0 0.00 0.0 0

CO 44.2700 28.010 0.07278 0.03222 55.7328 4339.8 2418.69 315.8 139.825

COS 0.0000 60.070 0.15608 0.00000 0.0000 0 0.00 0.0 0

Methane 0.0361 16.043 0.04168 0.00002 0.0260 23911.2 6.22 996.7 0.35982

Total: 99.86 Total Density 0.05781 100.0000 Gross Heating Value

Specific Gravity 0.75569 Btu/lb 4274 Btu/SCF 247.10

Net Heating Values

Btu/lb 3995 Btu/SCF 231

Net Heating Value (Lower Heating Value), Btu/lb, calculated as Gross Heating Value (Higher Heating Value) - 10.30 (%H2 x 8.94

CALCULATION OF F FACTORS 

Weight Percents

ComponentMol. Wt. C Factor H Factor % volume Fract. Wt. Carbon Hydrogen Nitrogen Oxygen

Hydrogen 2.016 0 1 33.460 67.4554 3.0318272

Oxygen 31.999 0 0 0.000 0.0000 0

Argon 39.948 0 0 0.700 27.9636

Nitrogen 28.014 0 0 3.280 91.8859 4.129875344

CO2 44.010 0.27291525 0 18.110 797.0211 9.77654925 26.0431

CO 28.010 0.42881114 0 44.270 1240.0027 23.8988313 32.0296

COS 60.070 0.19995006 0 0.000 0.0000 0 0

Methane 16.043 0.74867543 0.251325 0.036 0.5792 0.01948832 0.0065421

Totals 99.85610 2224.9078 33.6948689 3.04 4.129875344 58.0727

CALCULATED VALUES

O2 F Factor (dry), Fd 8534 DSCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air

Predicted Fo Factor 0.70 EPA Method 3a Fo value
APPENDIX D 

CEMS DATA 
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 10:46 38.34 17.6 10.8 827.7

01/08/2008 10:47 38.23 17.6 10.8 829.9

01/08/2008 10:48 37.99 17.6 10.8 822.6

01/08/2008 10:49 37.91 17.4 10.8 842

01/08/2008 10:50 38.22 17.5 10.8 834.7

01/08/2008 10:51 39.05 16.8 10.7 832.2

01/08/2008 10:52 37.92 16.6 10.7 843.2

01/08/2008 10:53 37.76 17.5 10.8 821

01/08/2008 10:54 38.59 17.5 10.8 827

01/08/2008 10:55 38.53 17.6 10.8 819.4

01/08/2008 10:56 38.57 17.8 10.8 842

01/08/2008 10:57 38.53 17.6 10.8 841

01/08/2008 10:58 38.67 17.5 10.7 841.4

01/08/2008 10:59 39.01 17.5 10.8 848.6

01/08/2008 11:00 38.77 17.6 10.8 851.9

01/08/2008 11:01 38.44 17.9 10.8 832.5

01/08/2008 11:02 38.56 17.8 10.8 845.6

01/08/2008 11:03 38.89 17.6 10.7 828.7

01/08/2008 11:04 38.6 17.3 10.7 837.4

01/08/2008 11:05 38.94 17.1 10.7 839.4

01/08/2008 11:06 39.31 16.8 10.7 843.8

01/08/2008 11:07 38.21 16.5 10.7 862.8

01/08/2008 11:08 37.92 16.8 10.7 843

01/08/2008 11:09 38.58 16.8 10.7 844.2

01/08/2008 11:10 38.67 17 10.7 846.8

01/08/2008 11:11 38.43 17 10.7 852.1

01/08/2008 11:12 38.44 16.8 10.7 848.1

01/08/2008 11:13 38.62 16.9 10.7 839.3

01/08/2008 11:14 39.07 16.6 10.7 847

01/08/2008 11:15 39.7 16.8 10.7 843

01/08/2008 11:16 40.01 16.4 10.6 838.5

01/08/2008 11:17 38.89 16.1 10.7 834.3

01/08/2008 11:18 38.85 17.1 10.7 812

01/08/2008 11:19 39.2 17.3 10.7 838.6

01/08/2008 11:20 39.28 17.1 10.7 848.5

01/08/2008 11:21 39.47 17.2 10.7 844.5

01/08/2008 11:22 39.13 17.4 10.7 858.7

01/08/2008 11:23 38.82 17.5 10.7 833.7

01/08/2008 11:24 38.82 17.4 10.7 839.4

01/08/2008 11:25 38.71 17.3 10.7 846.4

Page 1 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 11:26 38.92 17.6 10.8 839.8

01/08/2008 11:27 38.72 17.6 10.8 843.9

01/08/2008 11:28 38.37 17.3 10.8 851.1

01/08/2008 11:29 38.56 17.7 10.7 837.4

01/08/2008 11:30 38.82 17.1 10.7 844.4

01/08/2008 11:31 39.44 16.4 10.7 850.7

01/08/2008 11:32 38.04 16.6 10.7 841.4

01/08/2008 11:33 37.89 17.3 10.7 855

01/08/2008 11:34 38.42 17.1 10.7 860.6

01/08/2008 11:35 38.63 17.2 10.7 832.7

01/08/2008 11:36 38.25 17.1 10.7 828.6

01/08/2008 11:37 38.69 16.9 10.7 835.9

01/08/2008 11:38 39.12 17 10.8 836.1

01/08/2008 11:39 39.13 17.3 10.8 844.6

01/08/2008 11:40 39.38 17.4 10.7 844.4

01/08/2008 11:41 39.38 17.5 10.7 848.4

01/08/2008 11:42 39.11 17.5 10.7 842.5

01/08/2008 11:43 38.69 17.3 10.7 842.4

01/08/2008 11:44 38.6 17.3 10.7 841

01/08/2008 11:45 38.61 17.5 10.8 837.3

01/08/2008 11:46 39.1 17.2 10.7 838.3

01/08/2008 11:47 37.92 16.7 10.7 836.9

01/08/2008 11:48 37.53 17.2 10.8 849.9

01/08/2008 11:49 37.81 17.5 10.8 838.6

01/08/2008 11:50 38.32 17.5 10.8 835.9

01/08/2008 11:51 38.57 17.2 10.7 818.7

01/08/2008 11:52 38.97 16.9 10.8 826.8

01/08/2008 11:53 38.8 17.3 10.8 852.9

01/08/2008 11:54 39.21 17.2 10.8 840.1

01/08/2008 11:55 39.28 17.5 10.8 837.4

01/08/2008 11:56 39.69 17 10.7 825.1

01/08/2008 11:57 38.74 16.8 10.7 833.6

01/08/2008 11:58 38.1 17.5 10.8 848.9

01/08/2008 11:59 38.63 17.5 10.7 849

01/08/2008 12:00 38.77 17.3 10.7 838.5

01/08/2008 12:01 38.81 17.2 10.7 830.3

01/08/2008 12:02 38.5 16.9 10.7 842.3

01/08/2008 12:03 38.64 17.1 10.8 845.3

01/08/2008 12:04 39.11 17.2 10.7 840.8

01/08/2008 12:05 38.8 17.4 10.8 864.7

Page 2 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 12:06 39.17 17.3 10.8 850.8

01/08/2008 12:07 39.31 17.3 10.8 846.9

01/08/2008 12:08 39.22 17.3 10.7 830.6

01/08/2008 12:09 39.22 17 10.7 845.6

01/08/2008 12:10 39.68 17 10.7 863.5

01/08/2008 12:11 39.83 16.7 10.7 835.6

01/08/2008 12:12 38.42 16.7 10.7 833.7

01/08/2008 12:13 38.16 17.3 10.8 827.9

01/08/2008 12:14 38.85 17.3 10.8 842.8

01/08/2008 12:15 38.82 17.1 10.8 844.5

01/08/2008 12:16 38.77 17.4 10.7 850.4

01/08/2008 12:17 38.99 17.1 10.8 835.9

01/08/2008 12:18 38.99 17.5 10.8 859.3

01/08/2008 12:19 38.96 17.6 10.8 841.9

01/08/2008 12:20 39.06 17.6 10.7 845.4

01/08/2008 12:21 39.03 17.1 10.7 833

01/08/2008 12:22 38.87 16.9 10.7 851.8

01/08/2008 12:23 38.85 16.7 10.7 813.8

01/08/2008 12:24 39.17 16.8 10.7 830.4

01/08/2008 12:25 39.61 17 10.7 836.5

01/08/2008 12:26 36.76 12.8 10.6 847.8

01/08/2008 12:27 6.89 0.4 10.7 851.3

01/08/2008 12:28 16.8 10.2 10.7 840.3

01/08/2008 12:29 36.9 16.3 10.7 833.5

01/08/2008 12:30 38.52 16.4 10.7 830.5

01/08/2008 12:31 38.82 16.1 10.7 832.3

01/08/2008 12:32 39.09 16.2 10.7 830.3

01/08/2008 12:33 38.96 16.5 10.7 829.4

01/08/2008 12:34 39.27 16.7 10.7 836.6

01/08/2008 12:35 39.5 16.7 10.7 837.9

01/08/2008 12:36 40.3 16.2 10.6 849.7

01/08/2008 12:37 39.46 16.1 10.7 843

01/08/2008 12:38 38.8 16.8 10.8 826.6

01/08/2008 12:39 39.1 17.1 10.8 836.2

01/08/2008 12:40 39.03 17.5 10.8 845.4

01/08/2008 12:41 38.76 17.1 10.7 850

01/08/2008 12:42 38.34 17 10.7 825.4

01/08/2008 12:43 37.78 17 10.8 783.5

01/08/2008 12:44 38.09 17.2 10.8 807

01/08/2008 12:45 37.67 17.5 10.8 822.4

Page 3 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 12:46 38.03 17.5 10.8 832

01/08/2008 12:47 38.06 17.3 10.8 840.5

01/08/2008 12:48 38.41 17.1 10.8 829.9

01/08/2008 12:49 38.1 17.1 10.8 836.5

01/08/2008 12:50 38.75 17.2 10.8 834.8

01/08/2008 12:51 39.23 16.7 10.7 825.5

01/08/2008 12:52 38.45 16.6 10.8 832.5

01/08/2008 12:53 37.97 17.3 10.8 841.4

01/08/2008 12:54 38.47 17.3 10.8 843

01/08/2008 12:55 38.68 17.3 10.8 845.4

01/08/2008 12:56 38.73 17.2 10.8 844.3

01/08/2008 12:57 38.55 17.3 10.8 836.3

01/08/2008 12:58 38.78 17.4 10.8 844.2

01/08/2008 12:59 38.56 17.4 10.8 860.4

01/08/2008 13:00 38.93 17.3 10.8 832.5

01/08/2008 13:01 38.69 17.7 10.8 837.7

01/08/2008 13:02 38.57 17.6 10.8 837

01/08/2008 13:03 38.42 17.8 10.8 854.2

01/08/2008 13:04 38.64 17.5 10.8 843.4

01/08/2008 13:05 38.3 17.5 10.8 849

01/08/2008 13:06 39.1 17 10.7 846.6

01/08/2008 13:07 38.13 16.5 10.8 838.8

01/08/2008 13:08 37.28 17.4 10.8 830.4

01/08/2008 13:09 37.17 17.6 10.8 828.3

01/08/2008 13:10 37.77 17.9 10.8 824.7

01/08/2008 13:11 37.72 17.8 10.8 827.1

01/08/2008 13:12 38.47 17.6 10.8 848.9

01/08/2008 13:13 38.22 17.5 10.8 840.1

01/08/2008 13:14 38.46 17.6 10.8 825.8

01/08/2008 13:15 38.28 17.6 10.8 836.9

01/08/2008 13:16 39 17.6 10.8 838.3

01/08/2008 13:17 38.26 17.1 10.8 844.8

01/08/2008 13:18 38.05 17.9 10.8 836.1

01/08/2008 13:19 38.49 17.5 10.8 852.5

01/08/2008 13:20 38.54 17.5 10.8 826.8

01/08/2008 13:21 38.42 17.6 10.8 824.3

01/08/2008 13:22 38.75 17.7 10.8 852.2

01/08/2008 13:23 38.47 17.8 10.8 863.8

01/08/2008 13:24 38.7 17.7 10.8 839

01/08/2008 13:25 38.3 17.2 10.8 834.5

Page 4 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 13:26 38.68 17.3 10.8 836.3

01/08/2008 13:27 38.16 17.2 10.8 838.5

01/08/2008 13:28 38.2 17.5 10.8 844.7

01/08/2008 13:29 38.35 17.5 10.8 800.8

01/08/2008 13:30 38.43 17.7 10.8 837.1

01/08/2008 13:31 39.03 17.1 10.7 825.2

01/08/2008 13:32 38.22 16.5 10.8 852.3

01/08/2008 13:33 37.85 17 10.8 863.4

01/08/2008 13:34 38.27 17.3 10.8 830.5

01/08/2008 13:35 37.9 17.4 10.8 836.8

01/08/2008 13:36 38.12 17.5 10.8 837.5

01/08/2008 13:37 38.21 17.6 10.8 844

01/08/2008 13:38 38.32 17.7 10.8 844

01/08/2008 13:39 38.37 17.4 10.8 822.3

01/08/2008 13:40 38.66 17.4 10.8 833

01/08/2008 13:41 38.77 17.3 10.8 828.4

01/08/2008 13:42 38.63 17.3 10.8 839.1

01/08/2008 13:43 38.71 17.2 10.7 846.1

01/08/2008 13:44 39.17 17 10.7 843

01/08/2008 13:45 39 17 10.7 842.9

01/08/2008 13:46 39.82 16.8 10.7 814.3

01/08/2008 13:47 38.69 16.2 10.7 853.6

01/08/2008 13:48 38.29 16.7 10.7 850.1

01/08/2008 13:49 39.01 16.6 10.7 845.6

01/08/2008 13:50 39.3 16.6 10.7 843.8

01/08/2008 13:51 39.14 16.8 10.7 842.7

01/08/2008 13:52 39.33 16.8 10.7 852.2

01/08/2008 13:53 39.4 16.8 10.8 825.7

01/08/2008 13:54 40.04 16.9 10.8 839.8

01/08/2008 13:55 40.29 17.1 10.8 842.3

01/08/2008 13:56 41.06 16.9 10.7 842.6

01/08/2008 13:57 39.72 16.7 10.8 832.8

01/08/2008 13:58 38.97 17.5 10.8 834.1

01/08/2008 13:59 39.95 17.6 10.8 822.3

01/08/2008 14:00 39.59 17.5 10.8 838.8

01/08/2008 14:01 39.4 17.5 10.8 839.3

01/08/2008 14:02 39.17 17.2 10.8 850.2

01/08/2008 14:03 38.83 17.4 10.8 841.3

01/08/2008 14:04 38.75 17.6 10.8 822.3

01/08/2008 14:05 38.73 17.9 10.8 830.6

Page 5 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 14:06 39.04 17.6 10.8 845.2

01/08/2008 14:07 39.16 17.4 10.8 842.9

01/08/2008 14:08 39.59 17.4 10.8 811.1

01/08/2008 14:09 39.06 17.4 10.8 825.7

01/08/2008 14:10 39.74 17.3 10.8 843.7

01/08/2008 14:11 40.66 17 10.7 839.1

01/08/2008 14:12 39.63 16.2 10.8 845

01/08/2008 14:13 38.85 17 10.8 841.8

01/08/2008 14:14 39.29 17.4 10.8 861.2

01/08/2008 14:15 39.51 17.6 10.8 843.6

01/08/2008 14:16 39.59 17.8 10.8 828.9

01/08/2008 14:17 39.89 17.4 10.8 834.8

01/08/2008 14:18 40.03 17.2 10.8 830.3

01/08/2008 14:19 40.31 17.5 10.8 847.1

01/08/2008 14:20 40.15 17.5 10.8 838.3

01/08/2008 14:21 40.38 17.8 10.8 830.4

01/08/2008 14:22 39.94 17.6 10.8 852

01/08/2008 14:23 39.59 17.7 10.8 848.9

01/08/2008 14:24 39.84 17.5 10.8 839.9

01/08/2008 14:25 39.69 17.4 10.8 831.1

01/08/2008 14:26 39.95 17.2 10.7 827.4

01/08/2008 14:27 38.73 16.6 10.8 844

01/08/2008 14:28 37.77 17.1 10.8 854.1

01/08/2008 14:29 38.53 17.5 10.8 858

01/08/2008 14:30 38.63 17.6 10.8 847.8

01/08/2008 14:31 38.82 17.5 10.8 834.2

01/08/2008 14:32 38.91 17 10.8 831.4

01/08/2008 14:33 39.28 17.3 10.8 847

01/08/2008 14:34 39.73 17.3 10.8 835.9

01/08/2008 14:35 40 16.9 10.8 852

01/08/2008 14:36 40.91 16.9 10.7 831.5

01/08/2008 14:37 40.27 16.3 10.8 826.1

01/08/2008 14:38 39.58 17.3 10.8 843.9

01/08/2008 14:39 39.46 17.4 10.8 847

01/08/2008 14:40 40.06 17.5 10.8 834.2

01/08/2008 14:41 40 17.3 10.8 836.4

01/08/2008 14:42 39.5 17.1 10.8 858.7

01/08/2008 14:43 39.27 17.3 10.8 832.3

01/08/2008 14:44 39.25 17.6 10.8 845.6

01/08/2008 14:45 39.01 17.5 10.8 821.9

Page 6 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 14:46 38.92 17.2 10.8 830.5

01/08/2008 14:47 39.02 17 10.8 842.9

01/08/2008 14:48 38.88 17.2 10.8 831.5

01/08/2008 14:49 38.82 17.3 10.8 833.9

01/08/2008 14:50 38.85 17.2 10.8 832.2

01/08/2008 14:51 39.62 17.3 10.7 843.5

01/08/2008 14:52 38.78 16.7 10.8 816.4

01/08/2008 14:53 38.18 17.4 10.8 831.3

01/08/2008 14:54 38.94 17.1 10.8 827.7

01/08/2008 14:55 39.11 17.2 10.8 846.4

01/08/2008 14:56 38.9 17.2 10.8 841.9

01/08/2008 14:57 39.23 16.9 10.7 849.5

01/08/2008 14:58 39.16 17 10.7 850.7

01/08/2008 14:59 39.39 17 10.7 852.5

01/08/2008 15:00 39.49 17 10.7 856.8

01/08/2008 15:01 39.56 16.8 10.7 849.7

01/08/2008 15:02 39.06 16.8 10.7 858.2

01/08/2008 15:03 38.96 17 10.7 822.9

01/08/2008 15:04 38.39 17.1 10.7 861

01/08/2008 15:05 38.85 16.8 10.7 866.3

01/08/2008 15:06 39.4 16.4 10.6 847.9

01/08/2008 15:07 38.53 15.8 10.7 849

01/08/2008 15:08 37.97 16.4 10.7 830.7

01/08/2008 15:09 38.36 16.6 10.7 857.9

01/08/2008 15:10 38.78 16.7 10.8 876.1

01/08/2008 15:11 38.94 16.8 10.7 868.6

01/08/2008 15:12 39.42 17 10.8 863.7

01/08/2008 15:13 39.24 17.2 10.8 868.1

01/08/2008 15:14 39.58 17.2 10.8 845.1

01/08/2008 15:15 39.76 17.1 10.8 859.5

01/08/2008 15:16 40.01 16.8 10.7 843.6

01/08/2008 15:17 39.16 16.3 10.8 813.8

01/08/2008 15:18 38.14 17.2 10.8 811.4

01/08/2008 15:19 38.29 17.4 10.8 835

01/08/2008 15:20 38.45 17 10.8 824.3

01/08/2008 15:21 38.69 16.9 10.7 839.2

01/08/2008 15:22 38.19 16.8 10.8 808.2

01/08/2008 15:23 38.02 17.2 10.8 827.2

01/08/2008 15:24 37.63 17.5 10.8 850.6

01/08/2008 15:25 38.05 17.1 10.8 853.3

Page 7 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 15:26 38.27 17.3 10.8 847.3

01/08/2008 15:27 37.75 17.3 10.8 851.9

01/08/2008 15:28 37.59 17.2 10.7 844.1

01/08/2008 15:29 37.85 16.9 10.8 839.2

01/08/2008 15:30 38.34 17 10.8 846.1

01/08/2008 15:31 38.98 16.9 10.7 859

01/08/2008 15:32 38.61 16.1 10.7 859.8

01/08/2008 15:33 38.03 16.7 10.7 855.1

01/08/2008 15:34 38.91 16.7 10.7 853.1

01/08/2008 15:35 39.23 16.6 10.7 858.6

01/08/2008 15:36 39.05 16.5 10.7 857.9

01/08/2008 15:37 38.99 16.4 10.7 853.5

01/08/2008 15:38 38.8 16.7 10.7 837.6

01/08/2008 15:39 39.32 16.8 10.7 834.8

01/08/2008 15:40 39.23 16.7 10.7 836.8

01/08/2008 15:41 39.23 16.6 10.7 836.6

01/08/2008 15:42 38.84 16.3 10.7 834.6

01/08/2008 15:43 38.6 16.4 10.7 829.3

01/08/2008 15:44 38.66 16.4 10.7 837.2

01/08/2008 15:45 38.56 16.6 10.7 851.2

01/08/2008 15:46 38.9 16.6 10.7 827.2

01/08/2008 15:47 37.92 16.1 10.7 830.9

01/08/2008 15:48 37.51 17 10.8 868.5

01/08/2008 15:49 37.98 17.2 10.7 830.7

01/08/2008 15:50 38.56 16.8 10.7 841

01/08/2008 15:51 39.28 16.8 10.7 842.1

01/08/2008 15:52 39.25 16.5 10.8 837.7

01/08/2008 15:53 39.38 16.8 10.8 854.9

01/08/2008 15:54 39.31 16.9 10.8 825.5

01/08/2008 15:55 39.75 17 10.8 822.6

01/08/2008 15:56 40.11 16.9 10.7 817.4

01/08/2008 15:57 39.52 16.3 10.8 832.1

01/08/2008 15:58 38.13 16.9 10.8 820.7

01/08/2008 15:59 38.29 17 10.8 826.9

01/08/2008 16:00 37.72 17.2 10.8 822.9

01/08/2008 16:01 37.51 17.2 10.8 839

01/08/2008 16:02 36.84 17 10.8 856.6

01/08/2008 16:03 36.94 17.3 10.8 853

01/08/2008 16:04 37.13 17.4 10.8 827.1

01/08/2008 16:05 37.53 17.5 10.8 820.3

Page 8 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 16:06 37.28 17.5 10.8 824

01/08/2008 16:07 37.7 17.2 10.8 828.9

01/08/2008 16:08 37.35 17.1 10.8 824.4

01/08/2008 16:09 37.61 17.2 10.8 830.4

01/08/2008 16:10 37.65 17.4 10.8 829.5

01/08/2008 16:11 38.39 17.2 10.7 830.9

01/08/2008 16:12 37.69 16.3 10.8 824.3

01/08/2008 16:13 36.59 16.9 10.8 838.3

01/08/2008 16:14 36.92 16.9 10.8 837.3

01/08/2008 16:15 37.15 16.6 10.7 823.2

01/08/2008 16:16 37.17 16.6 10.7 825.6

01/08/2008 16:17 37.24 16.4 10.7 835.6

01/08/2008 16:18 37.62 16.4 10.7 848.2

01/08/2008 16:19 37.98 16.3 10.7 844

01/08/2008 16:20 38.6 16.5 10.7 828.6

01/08/2008 16:21 38.57 16.3 10.7 814.5

01/08/2008 16:22 39.16 16 10.7 821.6

01/08/2008 16:23 39.37 15.6 10.7 824.7

01/08/2008 16:24 38.93 15.8 10.7 833.5

01/08/2008 16:25 39.05 15.9 10.7 815.4

01/08/2008 16:26 39.86 16.1 10.7 806.3

01/08/2008 16:27 39.64 15.5 10.7 819.7

01/08/2008 16:28 38.14 16.2 10.7 810

01/08/2008 16:29 38.61 16.4 10.7 802.6

01/08/2008 16:30 38.55 16.6 10.7 818.5

01/08/2008 16:31 38.41 16.6 10.7 849.1

01/08/2008 16:32 38.1 16.5 10.7 840

01/08/2008 16:33 37.65 16.6 10.8 838.2

01/08/2008 16:34 36.94 16.9 10.8 832

01/08/2008 16:35 36.76 16.8 10.8 840.9

01/08/2008 16:36 38.07 16.8 10.7 810.4

01/08/2008 16:37 37.33 15.8 10.7 834.3

01/08/2008 16:38 36.31 16.8 10.8 851.9

01/08/2008 16:39 36.55 16.9 10.8 848

01/08/2008 16:40 36.72 16.7 10.8 818.5

01/08/2008 16:41 36.92 16.6 10.7 837.7

01/08/2008 16:42 37.25 16.3 10.7 799.8

01/08/2008 16:43 37.38 16.6 10.7 826.9

01/08/2008 16:44 37.32 16.5 10.8 833.1

01/08/2008 16:45 37.99 16.5 10.7 837.7

Page 9 of 10
SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1

01/08/2008 16:46 37.91 16.5 10.7 831.5

01/08/2008 16:47 38.08 16.6 10.8 822.2

01/08/2008 16:48 37.47 16.5 10.8 828.9

01/08/2008 16:49 37.45 16.6 10.8 825.2

01/08/2008 16:50 37.36 16.6 10.7 825.6

01/08/2008 16:51 37.95 16.5 10.7 822.3

01/08/2008 16:52 37.37 15.6 10.7 827.4

01/08/2008 16:53 36.37 16.3 10.8 823.1

01/08/2008 16:54 36.53 16.6 10.8 840.9

01/08/2008 16:55 36.8 16.9 10.8 798.7

01/08/2008 16:56 36.51 16.9 10.8 823.1

01/08/2008 16:57 37.03 16.8 10.7 816.6

01/08/2008 16:58 36.96 16.6 10.8 810.3

01/08/2008 16:59 37.09 16.7 10.8 827.4

01/08/2008 17:00 36.73 16.8 10.8 833

Averages: 38.493 16.97 10.76 837.87

Page 10 of 10
APPENDIX E 

VISIBLE EMISSIONS DATA SHEET 

APPENDIX F 

TEST PARTICIPANTS 
TEST PARTICIPANTS

AIR SERVICES GROUP 

TEST TEAM

Jorge Varino Environmental Technician – Team Lead 

Gary Barber Associate Technician 

Scott Given Associate Technician 

Ryan Newell Associate Technician 

David A. Smith Coordinator, Air Services Group 

PROCESS DATA

Raymond A. McDarby Senior Environmental Technician 

FUEL ANALYSIS

Bret Nicholas Lab Team Leader – Polk Power Station 

Raymond A. McDarby Senior Environmental Technician 

REPORT PREPARATION

Raymond A. McDarby Senior Environmental Technician 

QUALITY ASSURANCE / QUALITY CONTROL

Raymond A. McDarby Senior Environmental Technician 

POLK POWER STATION

Michael Perkins Environmental Coordinator 

Joshua Ellwein Principal Engineer