# EMISSIONS TEST REPORT

POLK POWER STATION FACILITY ID NUMBER: 1050233 EMISSION UNIT ID NO: -001 UNIT 1 SYNTHETIC GAS

CARBON MONOXIDE, VISIBLE EMISSIONS EVALUATION, and OXIDES OF NITROGEN, SULF UR DIOXIDE FROM CEMS

January 8, 2008

Prepared For: Tampa Electric Company Polk Power Station P.O. Box 111 Tampa, Florida 33601-0111

Prepared By: Tampa Electric Company Environmental, Health, & Safety Air Services Group

Environmental, Health, & Safety Air Services Group 5010 Causeway Boulevard Tampa, Florida 33619- 6130

## REPORT CERTIFICATION

The sampling and subseque nt data entry/reduction detailed in this report was conducted at my direction, and I here by certify that this test report is authentic and accurate to the best of my knowledge.

Signature:__________________________ Jorge A. Varino Environmental Technician Test Team Lead Air Services Group Environmental Health & Safety Tampa Electric Company

I have reviewed the test performa nce, associated quality assurance activities, the resultant calculations, and the contents of this report, and certify that all project quality obj ectives have been met. Th is report is approved for submittal.

Signature:__________________________ Raymond A. McDarby, Jr. Senior Environmental Technician Quality Assurance/Quality Control Specialist Air Services Group Environmental Health & Safety Tampa Electric Company

I have reviewed the testing details and results submitted in this report, and hereby certify that this test report is authenti c and accurate to the best of my knowledge.

Signature:__________________________ David A. Smith Coordinator – Air Services Group

Environmental Health & Safety Tampa Electric Company

## TABLE OF CONTENTS

SECTION PAGE NO. 1.0 INTRODUCTION 1 2.0 DISCUSSION OF RESULTS 2 EXECUTIVE SUMMARY 2 3.0 SOURCE DESCRIPTION/TEST PROCEDURES 4 4.0 TABULATED RESULTS CARBON MONOXIDE TEST DATA 6 NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 7 HEAT INPUT CALCULATIONS 8 5.0 STACK SAMPLING LOCATION DIAGRAM 10

APPENDICES

A. CARBON MONOXIDE TEST INFORMATION SUMMARIZED RUN DATA & QA/QC TEST RUN LOG CYLINDER GAS CERTIFICATES

B. TURBINE DATA C. FUEL ANALYSIS

D. CEMS DATA

E. VISIBLE EMISSION DATA SHEET

F. TEST PARTICIPANTS

### 1 

## 1.0 INTRODUCTION

On January 8, 2008, Tampa Elec tric Company’s, Environmental Services, Air Services Group performed Carbon Monoxide (CO), Vola tile Organic Compounds (VOC) source emission tests, and Visible Emissions Observ ations on Unit No. 1 at the Polk Power Station. Unit No. 1 is a combined cycle combustion turbine generating unit. The combustion turbine was fired with syngas from the solid fuel gasification system. A blend of petroleum coke and bituminous coal was gasified for this test. Testing was conducted according to United States Envi ronmental Protection Agency (USEPA) test methods stipulated in 40 CFR Part 60, Appendix A and Florida Department of Environmental Protection (FDEP) Permi t No. 1050233-016-AV. Testing was conducted concurrent with the annual 40CFR75 Relative A ccuracy Test Audit (RATA) for this unit.

Nitrogen Oxides (NO x 

### ) and Sulfur Dioxide (SO 2 

### ) data was taken from the Continuous Emissions Monitoring System’s (CEMS) Da ta Acquisition and Handling System (DAHS) and is presented as averages over the test period.

### 2 

## 2.0 DISCUSSION OF RESULTS

Executive Summary Tampa Electric Company Polk Power Station General Electric 7F Combined Cycle Combustion Turbine Emission Unit ID -001

Solid Fuel Derived Synthetic Gas Compliance Parameter Test Result FDEP Permit Limit CO, ppmvd @15% O2 4 25 CO, lbs/hr 16 98 VE, % opacity 0 10 NOX, lbs/hr 101.87 220.25 SO2, lbs/hr 321 357 Heat Input, mmBtu/hr 1717 -- Maximum Heat Input 1 1751 -- Unit Load (% of permit) 2 98% 90 – 100%

1 Maximum Heat Input is Permitted Maximum Heat Input Rate, 1755 mmBtu/hr @ 59o F, Corrected to Average Ambient Temperature Recorded During the Test Period.



### 2 Unit Load (% of permit) is Heat Input Divided by Maximum Heat Input times 100.



### The Carbon Monoxide (CO) concentration and em ission rate was derived from three 1- hour test runs. The calculated average CO concentration was 4 ppmvd @ 15% O 2 

### . The calculated average emission rate was 16 lbs/hr. The FDEP permitted concentration is 25 ppmvd @15% O 2 

### . The FDEP permitted emissi on rate is 98 lbs/hr based on a 30-day rolling average.

The Visible Emissions Observations (VEO ) yielded an average opacity of 0% for the 1- hour test. The FDEP permitted opacity is 10 percent.

During the CO testing, the Nitrogen Oxides (NO x 

### ) average emission rate was 101.87 lbs/hr.

During the CO testing, the Sulfur Dioxide (SO 2 

### ) average emission rate was 321 lbs/hr.

### 3 

### During the test Unit No. 1 was operated at an average heat input of 1717 mmBtu/hr. The FDEP permitted heat input is 1755 mmBtu/h r, at an ambient te mperature of 59o (corrected to 1751 mmBtu/hr based on an average inlet vane temperature of 77o F, and the manufacturer’s heat input correction curve for this unit). The unit operated at 98% of permitted capacity.

### 4 

## 3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generat ing Station is located at County Road 630 approximately 13 miles southwest of Bartow, Polk County, Florida. Unit No. 1 is a Combined Cycle Combustion Turbine generating unit, with a net capacity of 192 MW when fired with Syngas fuel. The source sampling location c onsists of a circular stack 19 feet in diameter with four sample ports located 90 degrees apart on the stack circumference. A diagram of the stack sampling locati on is included along wit h other pertinent information on the test site.

Carbon Monoxide sampling was performed in accordance with USEPA Reference Method 10 (40 CFR Part 60, Appendix A) “Determination of Carbon Monoxide Emissions From Stationary Sources”. Testing was performed using a Thermo Environmental Instruments model 48C Ca rbon Monoxide Analyzer. Testing was conducted concurrently with the annual USEPA 40CFR75 Relative Accuracy Test Audit (RATA) for this unit.

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. This data was taken as 1-minute averages ov er the time frame fr om 10:46 on January 8, 2008 through 17:00 on January 8, 2008, representing the time frame of the CO test.

Plant operational data was taken from the Pl ant Information (PI) se rver system. Data captured included the minute average load, minute fuel flow, minute inlet vane temperature, and minute saturator readi ngs from 10:46 on J anuary 8, 2008 through 17:00 on January 8, 2008.

### 5 

## 4.0 TABULATED RESULTS

## POLK POWER STATION CARBON MONOXIDE DAT A

CO % O 2 

### CO, ppmvd CO Run # Start Stop ppmvd volume @ 15% O 2 

### lbs/hr 1 10:46 12:20 6.48 11.51 4.07 15.37 2 12:39 13:00 6.40 11.54 4.03 15.23 3 13:14 13:35 6.24 11.58 3.95 14.91 4 13:48 14:09 6.37 11.52 4.01 15.13 5 14:19 14:40 6.31 11.57 3.99 15.06 6 14:55 15:16 6.67 11.53 4.20 15.86 7 15:32 15:53 6.79 11.53 4.28 16.14 8 16:07 16:28 7.00 11.46 4.38 16.52 9 16:39 17:00 6.87 11.50 4.31 16.28 Averages: 4.135 15.610 CO, ppmvd @ 15% O 2 

### is calculated as: CO, ppmvd x (5.9 / (20.9 - % O 2 

### , volume))

CO, lbs/hr is calculated as: CO, ppmvd x C f 

### x F d 

### x (20.9 / (20.9 - % O 2 

### , volume) x Heat Input

where: C f 

### = 7.27249E-08 lb/scf F d 

### = 8534 dscf/mmBtu Heat Input = 1717 mmBtu/hr Test Times RM Data Calculated Data 

### COMBINED CYCLE COMBUSTION TURBINE UNIT 1 January 8, 2008

6

## POLK POWER STATION N O X 

## & S O 2 

## COMPLIANCE DATA FROM CEM S

NO x 

### SO 2 

### Flow NO x 

### SO 2 

### ppmvw ppmvw kscfmw lbs/hr lbs/hr

16.97 38.49 837.87 101.87 321

NOX, lbs/hr calculated as: NOX, ppmvw x 1.194E-07 x Flow, kscfmw x 60 min/hr x 1000/k

SO2, lbs/hr calculated as: SO2, ppmvw x 1.660E-07 x Flow, kscfmw x 60 min/hr x 1000/k 

### CEM Data Calculated Data COMBINED CYCLE COMBUSTION TURBINE UNIT 1 January 8, 2008

7

## POLK POWER STATION HEAT INPUT CALCULATIO N

Average fuel flow: 7124.8504 Kcfh M

ole weight correction to meter cal: 0.9883 mole weight correction factor Corrected fuel flow:1 7041.4897 Kcfh, corrected for density Average moisture: 1.31 % H 2 

### 0 added to fuel Corrected fuel flow:2 6949.1249 Kscfh, corrected for moisture Gross heating value of fuel (HHV): 247.10 Btu/scf Heat Input: 1717 mmBtu/hr

Average fuel flow from Plant Information Data Base. Mole weight correction factor to meter calibrat ion is taken from ratio of syngas mole weight to calibration gas mole weight. 1Average fuel flow times mole weight correction factor. 2Corrected fuel flow times (1 - (Average moisture / 100)). Gross Heating value of fuel (HHV) is from fuel analysis. Heat input is (HHV x Corrected fuel flow) / 1000. 

### COMBINED CYCLE COMBUSTION TURBINE UNIT 1 January 8, 2008

8

### 9 

## 5.0 SAMPLING LOCATION DIAGRAM

### 10 UNFIRED HEAT

RECOVERY

BOILER TRANSITION

DUCT

EXHAUST FROM TURBINE 14 FT.

38 FT. 150 FT.

136 FT. 

## POLK POWER STATION COMBUSTION TURBINE COMBINED CYCLE UNIT NO.1 TEST LOCATION

PORT LOCATION PLAN 19.0 FT.ID.

STACK DIAMETERS DOWNSTREAM FROM DISTURBANCE = 2.0 STACK DIAMETERS UPSTREAM FROM DISTURBANCE = 0.7 STACK DIAMETER = 19.0 FT. STACK AREA = 283.529 S Q . FT. STACK AREA =40828.138 SQ. IN.

## APPENDIX A

CARBON MONOXIDE TEST INFORMATION

### SUMMARIZED RUN DATA & QA/QCLabView QA Report

Polk Unit 1 CO Compliance - Report RUN 1 01/08/2008 10:46:01 12:20:09

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.047 0.044 0.001 Span 10.574 9.378 7.986 Final Readings Zero 0.07 0.085 0.032 Span 10.556 9.406 8.016

System Bias (Eq 7E-2) Initial Zero Bias SB -0.01 0.09 0.24 Initial Span Bias SB -0.01 1.3 -0.39 Final Zero Bias SB 0.1 0.32 0.62 Final Span Bias SB -0.1 1.46 -0.01

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.22 0.24 0.01 Initial Span SCE 0.35 2.1 -0.67 Final Zero SCE 0.33 0.47 0.4 Final Span SCE 0.27 2.26 -0.3

Drift Assessment (Eq 7E-4) Zero Drift D 0.11 0.23 0.38 Span Drift D 0.09 0.16 0.38

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.58 9.69 6.45 Corrected Results (ppmv) 11.51 9.29 6.48

Page 1 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 2 01/08/2008 12:39:43 13:00:44

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.07 0.085 0.032 Span 10.556 9.406 8.016 Final Readings Zero 0.075 0.058 -0.03 Span 10.549 9.341 7.916

System Bias (Eq 7E-2) Initial Zero Bias SB 0.1 0.32 0.62 Initial Span Bias SB -0.1 1.46 -0.01 Final Zero Bias SB 0.12 0.17 -0.12 Final Span Bias SB -0.13 1.09 -1.26

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.33 0.47 0.4 Initial Span SCE 0.27 2.26 -0.3 Final Zero SCE 0.36 0.32 -0.35 Final Span SCE 0.23 1.89 -1.54

Drift Assessment (Eq 7E-4) Zero Drift D 0.02 0.15 0.74 Span Drift D 0.03 0.37 1.25

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.59 9.68 6.34 Corrected Results (ppmv) 11.54 9.3 6.4

Page 2 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 3 01/08/2008 13:14:28 13:35:28

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.075 0.058 -0.03 Span 10.549 9.341 7.916 Final Readings Zero 0.07 0.081 -0.03 Span 10.508 9.333 7.917

System Bias (Eq 7E-2) Initial Zero Bias SB 0.12 0.17 -0.12 Initial Span Bias SB -0.13 1.09 -1.26 Final Zero Bias SB 0.1 0.29 -0.12 Final Span Bias SB -0.33 1.05 -1.24

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.36 0.32 -0.35 Initial Span SCE 0.23 1.89 -1.54 Final Zero SCE 0.33 0.45 -0.35 Final Span SCE 0.04 1.85 -1.53

Drift Assessment (Eq 7E-4) Zero Drift D 0.02 0.12 0 Span Drift D 0.2 0.04 0.02

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.6 9.65 6.14 Corrected Results (ppmv) 11.58 9.3 6.24

Page 3 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 4 01/08/2008 13:48:37 14:09:38

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.07 0.081 -0.03 Span 10.508 9.333 7.917 Final Readings Zero 0.047 0.044 0.001 Span 10.574 9.378 7.986

System Bias (Eq 7E-2) Initial Zero Bias SB 0.1 0.29 -0.12 Initial Span Bias SB -0.33 1.05 -1.24 Final Zero Bias SB -0.01 0.09 0.24 Final Span Bias SB -0.01 1.3 -0.39

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.33 0.45 -0.35 Initial Span SCE 0.04 1.85 -1.53 Final Zero SCE 0.22 0.24 0.01 Final Span SCE 0.35 2.1 -0.67

Drift Assessment (Eq 7E-4) Zero Drift D 0.11 0.2 0.36 Span Drift D 0.32 0.25 0.85

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.56 9.64 6.3 Corrected Results (ppmv) 11.52 9.28 6.37

Page 4 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 5 01/08/2008 14:19:50 14:40:51

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.052 0.048 -0.03 Span 10.495 9.276 7.906 Final Readings Zero 0.034 0.013 -0.16 Span 10.5 9.219 7.917

System Bias (Eq 7E-2) Initial Zero Bias SB 0.01 0.11 -0.12 Initial Span Bias SB -0.39 0.73 -1.38 Final Zero Bias SB -0.08 -0.08 -1.75 Final Span Bias SB -0.37 0.42 -1.24

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.25 0.27 -0.35 Initial Span SCE -0.02 1.53 -1.67 Final Zero SCE 0.16 0.07 -1.98 Final Span SCE 0 1.22 -1.53

Drift Assessment (Eq 7E-4) Zero Drift D 0.09 0.19 1.63 Span Drift D 0.02 0.31 0.14

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.56 9.64 6.19 Corrected Results (ppmv) 11.57 9.38 6.31

Page 5 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 6 01/08/2008 14:55:35 15:16:35

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.034 0.013 -0.16 Span 10.5 9.219 7.917 Final Readings Zero 0.032 0.05 0.011 Span 10.488 9.201 7.956

System Bias (Eq 7E-2) Initial Zero Bias SB -0.08 -0.08 -1.75 Initial Span Bias SB -0.37 0.42 -1.24 Final Zero Bias SB -0.09 0.12 0.36 Final Span Bias SB -0.43 0.32 -0.76

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.16 0.07 -1.98 Initial Span SCE 0 1.22 -1.53 Final Zero SCE 0.15 0.28 0.14 Final Span SCE -0.06 1.12 -1.04

Drift Assessment (Eq 7E-4) Zero Drift D 0.01 0.2 2.11 Span Drift D 0.06 0.1 0.48

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.52 9.54 6.57 Corrected Results (ppmv) 11.53 9.32 6.67

Page 6 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 7 01/08/2008 15:32:57 15:53:57

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.032 0.05 0.011 Span 10.488 9.201 7.956 Final Readings Zero 0.029 -0.009 -0.13 Span 10.483 9.176 7.946

System Bias (Eq 7E-2) Initial Zero Bias SB -0.09 0.12 0.36 Initial Span Bias SB -0.43 0.32 -0.76 Final Zero Bias SB -0.1 -0.21 -1.38 Final Span Bias SB -0.45 0.18 -0.88

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.15 0.28 0.14 Initial Span SCE -0.06 1.12 -1.04 Final Zero SCE 0.14 -0.05 -1.6 Final Span SCE -0.08 0.98 -1.17

Drift Assessment (Eq 7E-4) Zero Drift D 0.01 0.33 1.74 Span Drift D 0.02 0.14 0.12

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.51 9.54 6.71 Corrected Results (ppmv) 11.53 9.35 6.79

Page 7 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 8 01/08/2008 16:07:43 16:28:44

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.029 -0.009 -0.13 Span 10.483 9.176 7.946 Final Readings Zero 0.047 0.044 0.001 Span 10.574 9.378 7.986

System Bias (Eq 7E-2) Initial Zero Bias SB -0.1 -0.21 -1.38 Initial Span Bias SB -0.45 0.18 -0.88 Final Zero Bias SB -0.01 0.09 0.24 Final Span Bias SB -0.01 1.3 -0.39

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.14 -0.05 -1.6 Initial Span SCE -0.08 0.98 -1.17 Final Zero SCE 0.22 0.24 0.01 Final Span SCE 0.35 2.1 -0.67

Drift Assessment (Eq 7E-4) Zero Drift D 0.09 0.3 1.62 Span Drift D 0.44 1.12 0.49

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.49 9.51 6.93 Corrected Results (ppmv) 11.46 9.23 7

Page 8 of 9LabView QA Report

Polk Unit 1 CO Compliance - Report RUN 9 01/08/2008 16:39:22 17:00:23

Analyzer Calibration Error (Eq 7E-1) aO2 bCO2 cCO Analyzer Range 250 200 10 Units % PPM PPM Low Level Certified Value (PPM or %) Mid Level Certified Value (PPM or %) 10.5 9 3.94 High Level Certified Value (PPM or %) 20.9 18 8.04 Zero Level Observed 0.05 0.028 -0.02 Low Level Observed

- - - Mid Level Observed 10.577 9.144 4.074 High Level Observed 20.971 17.983 8.017 Zero Calibration Error ACE 0.24 0.16 -0.22 Low Level Calibration Error ACE 0 0 0 Mid Level Calibration Error ACE 0.37 0.8 1.67 High Level Calibration Error ACE 0.34 -0.09 -0.29 Initial Readings Zero 0.029 0.05 -0.11 Span 10.455 9.16 7.976 Final Readings Zero 0.047 0.044 0.001 Span 10.574 9.378 7.986

System Bias (Eq 7E-2) Initial Zero Bias SB -0.1 0.12 -1.13 Initial Span Bias SB -0.58 0.09 -0.51 Final Zero Bias SB -0.01 0.09 0.24 Final Span Bias SB -0.01 1.3 -0.39

System Calibration Error (Eq 7E-3) Initial Zero SCE 0.14 0.28 -1.36 Initial Span SCE -0.22 0.89 -0.8 Final Zero SCE 0.22 0.24 0.01 Final Span SCE 0.35 2.1 -0.67

Drift Assessment (Eq 7E-4) Zero Drift D 0.09 0.03 1.37 Span Drift D 0.57 1.21 0.12

Effluent Gas Concentration (Eq 7E-5) Raw Results 11.51 9.49 6.81 Corrected Results (ppmv) 11.5 9.22 6.87

Page 9 of 9

### TEST RUN LOG

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 7:13:59 AM 21.09 -0.04 0.17 01/08/2008 7:14:29 AM 21.08 -0.04 0.14 01/08/2008 7:14:59 AM 21.08 -0.04 0.15 01/08/2008 7:15:29 AM 21.07 -0.03 0.1 01/08/2008 7:15:59 AM 21.1 -0.04 -0.18 01/08/2008 7:16:29 AM 21.11 -0.05 -0.06 01/08/2008 7:16:59 AM 21.1 -0.03 0.03 01/08/2008 7:17:29 AM 21.09 -0.04 0.05 01/08/2008 7:17:59 AM 21.1 -0.03 0.01 01/08/2008 7:18:29 AM 21.1 -0.03 0.02 01/08/2008 7:18:59 AM 21.09 -0.04 0.01 01/08/2008 7:19:29 AM 21.08 -0.02 0 01/08/2008 7:19:59 AM 21.05 -0.02 0.01 01/08/2008 7:20:29 AM 21.06 -0.01 0 01/08/2008 7:20:59 AM 21.07 -0.02 0.01 01/08/2008 7:21:29 AM 21.07 -0.02 -0.01 01/08/2008 7:21:59 AM 21.06 -0.01 0.03 01/08/2008 7:22:29 AM 21.06 -0.01 -0.02 01/08/2008 7:22:59 AM 21.06 -0.01 -0.01 01/08/2008 7:23:29 AM 21.06 -0.01 -0.01 01/08/2008 7:23:59 AM 21.07 -0.01 -0.02 01/08/2008 7:24:29 AM 21.07 -0.01 0 01/08/2008 7:24:59 AM 21.06 0 -0.01 01/08/2008 7:25:29 AM 21.05 0 0.01 01/08/2008 7:25:59 AM 21.06 -0.01 -0.01 01/08/2008 7:26:29 AM 21.05 0 -0.01 01/08/2008 7:26:59 AM 21.05 0 -0.01 01/08/2008 7:27:29 AM 21.05 0 0.02 01/08/2008 7:27:59 AM 21.07 -0.01 -0.05 01/08/2008 7:28:29 AM 21.09 -0.04 -0.2 01/08/2008 7:28:59 AM 21.1 -0.05 -0.21 01/08/2008 7:29:29 AM 21.1 -0.05 -0.24 01/08/2008 7:29:59 AM 21.09 -0.04 -0.11 01/08/2008 7:30:29 AM 21.08 -0.02 -0.1 01/08/2008 7:30:59 AM 21.07 -0.02 -0.11 01/08/2008 7:31:29 AM 21.08 -0.03 -0.12 01/08/2008 7:31:59 AM 21.06 -0.02 -0.15 01/08/2008 7:32:29 AM 21.07 -0.03 -0.13 01/08/2008 7:32:59 AM 21.07 -0.02 -0.16 01/08/2008 7:33:29 AM 21.06 -0.02 -0.14



### Page 1 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 7:33:59 AM 21.06 -0.02 -0.19 01/08/2008 7:34:29 AM 21.07 -0.02 -0.16 01/08/2008 7:34:59 AM 21.06 -0.01 -0.18 01/08/2008 7:35:29 AM 21.06 -0.01 -0.19 01/08/2008 7:35:59 AM 21.06 -0.02 -0.19 01/08/2008 7:36:29 AM 21.07 -0.02 -0.2 01/08/2008 7:36:59 AM 21.06 -0.01 -0.19 01/08/2008 7:37:29 AM 21.06 -0.01 -0.21 01/08/2008 7:37:59 AM 21.06 -0.01 -0.24 01/08/2008 7:38:29 AM 12.19 5.32 -0.24 01/08/2008 7:38:59 AM 10.64 8.82 -0.24 01/08/2008 7:39:29 AM 10.65 8.91 -0.24 01/08/2008 7:39:59 AM 10.65 8.93 -0.24 01/08/2008 7:40:29 AM Linearity Check 10.64 8.95 -0.24 01/08/2008 7:40:59 AM Linearity Check 10.65 8.96 -0.02 01/08/2008 7:41:29 AM Linearity Check 10.66 8.97 -0.01 01/08/2008 7:41:59 AM Linearity Check 10.74 8.97 0.15 01/08/2008 7:42:29 AM Linearity Check 20.88 0.53 0.49 01/08/2008 7:42:59 AM Linearity Check 21.1 -0.04 0.42 01/08/2008 7:43:29 AM Linearity Check 20.01 5.99 -0.17 01/08/2008 7:43:59 AM Linearity Check 19.98 12.46 -0.24 01/08/2008 7:44:29 AM Linearity Check 21.06 17.12 -0.24 01/08/2008 7:44:59 AM Linearity Check 21.12 17.6 -0.24 01/08/2008 7:45:29 AM Linearity Check 21.14 17.65 -0.24 01/08/2008 7:45:59 AM Linearity Check 21.15 17.69 -0.24 01/08/2008 7:46:29 AM Linearity Check 21.16 17.99 -0.24 01/08/2008 7:46:59 AM Linearity Check 21.01 18.01 -0.24 01/08/2008 7:47:29 AM Linearity Check 20.97 18.01 -0.24 01/08/2008 7:47:59 AM Linearity Check 18.94 17.34 -0.2 01/08/2008 7:48:29 AM Linearity Check 10.66 9.33 -0.05 01/08/2008 7:48:59 AM Linearity Check 10.57 9.15 -0.04 01/08/2008 7:49:29 AM Linearity Check 10.58 9.14 -0.04 01/08/2008 7:49:59 AM Linearity Check 10.38 9.13 3.21 01/08/2008 7:50:29 AM Linearity Check 0.56 0.62 7.9 01/08/2008 7:50:59 AM Linearity Check 0.07 -0.05 8.01 01/08/2008 7:51:29 AM Linearity Check 0.05 -0.07 8.03 01/08/2008 7:51:59 AM Linearity Check 0.05 -0.03 8 01/08/2008 7:52:29 AM Linearity Check 0.05 0.04 8.02 01/08/2008 7:52:59 AM Linearity Check 0.04 0.02 7.34 01/08/2008 7:53:29 AM Linearity Check 0.25 0.01 4.28



### Page 2 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 7:53:59 AM Linearity Check 0.05 0.01 4.11 01/08/2008 7:54:29 AM Linearity Check 0.04 0.02 4.12 01/08/2008 7:54:59 AM Linearity Check 0.03 0.02 4.07 01/08/2008 7:55:29 AM Linearity Check 0.05 0.02 4.45 01/08/2008 7:55:59 AM Linearity Check 0.05 0.01 7.71 01/08/2008 7:56:29 AM Linearity Check 0.04 0.01 7.92 01/08/2008 7:56:59 AM Linearity Check 0.04 0.01 7.93 01/08/2008 7:57:29 AM Linearity Check 0.05 0.01 8.03 01/08/2008 7:57:59 AM Linearity Check 0.03 0.01 7.33 01/08/2008 7:58:29 AM Linearity Check 0.94 1.53 0.57 01/08/2008 7:58:59 AM Linearity Check 0.08 2.81 -0.12 01/08/2008 7:59:29 AM Linearity Check 0.02 3.66 -0.14 01/08/2008 7:59:59 AM Linearity Check 0.02 3.71 -0.15 01/08/2008 8:00:29 AM Linearity Check 0.02 3.73 -0.14 01/08/2008 8:00:59 AM Linearity Check 0.01 3.74 -0.16 01/08/2008 8:01:29 AM Linearity Check 0.01 3.74 -0.16 01/08/2008 8:01:59 AM Linearity Check 0.02 3.73 -0.16 01/08/2008 8:02:29 AM Linearity Check 0.02 3.74 -0.16 01/08/2008 8:02:59 AM Linearity Check 0.02 3.74 -0.16 01/08/2008 8:03:29 AM Linearity Check 0.01 3.74 -0.17 01/08/2008 8:03:59 AM Linearity Check 0.02 3.75 -0.17 01/08/2008 8:04:29 AM Linearity Check 0 3.75 -0.14 01/08/2008 8:04:59 AM Linearity Check 0.02 3.74 -0.16 01/08/2008 8:05:29 AM Linearity Check 0.02 3.75 -0.14 01/08/2008 8:05:59 AM Linearity Check 0.01 3.76 -0.18 01/08/2008 8:06:29 AM Linearity Check 0.02 3.75 -0.15 01/08/2008 8:06:59 AM Linearity Check 0.02 3.76 -0.17 01/08/2008 8:07:29 AM Linearity Check 0.02 3.75 -0.16 01/08/2008 8:07:59 AM Linearity Check 0.02 3.75 -0.17 01/08/2008 8:08:29 AM Linearity Check 0.02 3.75 -0.05 01/08/2008 8:08:59 AM Linearity Check 0.4 6.67 -0.03 01/08/2008 8:09:29 AM Linearity Check 0.01 8.06 -0.07 01/08/2008 8:09:59 AM Linearity Check 0 8.16 -0.06 01/08/2008 8:10:29 AM Linearity Check 0 8.16 -0.07 01/08/2008 8:10:59 AM Linearity Check 0 8.16 -0.08 01/08/2008 8:11:29 AM Linearity Check 0 8.17 -0.05 01/08/2008 8:11:59 AM Linearity Check 0 8.17 -0.08 01/08/2008 8:12:29 AM Linearity Check 0.01 8.16 -0.06 01/08/2008 8:12:59 AM Linearity Check 0.01 8.16 -0.08 01/08/2008 8:13:29 AM Linearity Check 9.66 6.29 0.53



### Page 3 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 8:13:59 AM Linearity Check 20.94 0.13 0.41 01/08/2008 8:14:29 AM Linearity Check 20.99 0.08 0.43 01/08/2008 8:14:59 AM Linearity Check 20.94 0.11 0.57 01/08/2008 8:15:29 AM Linearity Check 20.89 0.11 0.5 01/08/2008 8:15:59 AM Linearity Check 20.84 0.1 0.58 01/08/2008 8:16:29 AM Linearity Check 20.8 0.11 0.45 01/08/2008 8:16:59 AM converter check - 1 20.77 0.1 0.46 01/08/2008 8:17:29 AM converter check - 1 20.76 0.1 0.4 01/08/2008 8:17:59 AM converter check - 1 20.73 0.09 0.43 01/08/2008 8:18:29 AM converter check - 1 20.73 0.1 0.42 01/08/2008 8:18:59 AM converter check - 1 20.73 0.09 0.42 01/08/2008 8:19:29 AM converter check - 1 20.71 0.1 0.49 01/08/2008 8:19:59 AM converter check - 1 20.72 0.09 0.7 01/08/2008 8:20:29 AM converter check - 1 20.72 0.09 0.68 01/08/2008 8:20:59 AM converter check - 1 20.72 0.1 0.66 01/08/2008 8:21:29 AM converter check - 1 20.71 0.09 0.62 01/08/2008 8:21:59 AM converter check - 1 20.71 0.09 0.5 01/08/2008 8:22:29 AM converter check - 1 20.71 0.09 0.52 01/08/2008 8:22:59 AM converter check - 1 20.72 0.09 0.55 01/08/2008 8:23:29 AM converter check - 1 20.72 0.09 0.46 01/08/2008 8:23:59 AM converter check - 1 20.72 0.08 0.52 01/08/2008 8:24:29 AM converter check - 1 20.71 0.08 0.57 01/08/2008 8:24:59 AM converter check - 1 20.71 0.08 0.67 01/08/2008 8:25:29 AM converter check - 1 20.71 0.07 0.55 01/08/2008 8:25:59 AM converter check - 1 20.68 0.07 0.54 01/08/2008 8:26:29 AM converter check - 1 20.69 0.07 0.6 01/08/2008 8:26:59 AM converter check - 1 20.68 0.08 0.51 01/08/2008 8:27:29 AM converter check - 1 20.67 0.08 0.49 01/08/2008 8:27:59 AM converter check - 1 20.68 0.07 0.49 01/08/2008 8:28:29 AM converter check - 1 20.66 0.08 0.52 01/08/2008 8:28:59 AM converter check - 1 20.66 0.09 0.48 01/08/2008 8:29:29 AM converter check - 1 20.66 0.08 0.44 01/08/2008 8:29:59 AM converter check - 1 20.67 0.08 0.45 01/08/2008 8:30:29 AM converter check - 1 20.66 0.09 0.51 01/08/2008 8:30:59 AM converter check - 1 20.67 0.09 0.5 01/08/2008 8:31:29 AM converter check - 1 20.67 0.08 0.49 01/08/2008 8:31:59 AM converter check - 1 20.68 0.08 0.5 01/08/2008 8:32:29 AM converter check - 1 20.67 0.07 0.42 01/08/2008 8:32:59 AM converter check - 1 20.68 0.08 0.51 01/08/2008 8:33:29 AM converter check - 1 20.68 0.08 0.43



### Page 4 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 8:33:59 AM converter check - 1 20.67 0.08 0.46 01/08/2008 8:34:29 AM converter check - 1 20.69 0.07 0.57 01/08/2008 8:34:59 AM converter check - 1 20.7 0.08 0.67 01/08/2008 8:35:29 AM converter check - 1 20.71 0.07 0.72 01/08/2008 8:35:59 AM converter check - 1 20.71 0.07 0.77 01/08/2008 8:36:29 AM converter check - 1 20.72 0.07 0.6 01/08/2008 8:36:59 AM converter check - 1 20.72 0.06 0.52 01/08/2008 8:37:29 AM converter check - 1 20.71 0.06 0.53 01/08/2008 8:37:59 AM converter check - 1 20.72 0.06 0.51 01/08/2008 8:38:29 AM converter check - 1 20.71 0.07 0.55 01/08/2008 8:38:59 AM converter check - 1 20.71 0.07 0.54 01/08/2008 8:39:29 AM converter check - 1 20.72 0.07 0.51 01/08/2008 8:39:59 AM converter check - 1 20.71 0.07 0.56 01/08/2008 8:40:29 AM converter check - 1 20.7 0.06 0.71 01/08/2008 8:40:59 AM converter check - 1 20.71 0.05 0.74 01/08/2008 8:41:29 AM converter check - 1 20.7 0.06 0.72 01/08/2008 8:41:59 AM converter check - 1 20.7 0.06 0.67 01/08/2008 8:42:29 AM converter check - 1 20.7 0.06 0.54 01/08/2008 8:42:59 AM converter check - 1 20.68 0.06 0.68 01/08/2008 8:43:29 AM converter check - 1 20.68 0.07 0.66 01/08/2008 8:43:59 AM converter check - 1 20.68 0.07 0.64 01/08/2008 8:44:29 AM converter check - 1 20.7 0.06 0.77 01/08/2008 8:44:59 AM converter check - 1 20.69 0.07 0.72 01/08/2008 8:45:29 AM converter check - 1 20.69 0.07 0.66 01/08/2008 8:45:59 AM converter check - 1 20.69 0.06 0.75 01/08/2008 8:46:29 AM converter check - 1 20.69 0.05 0.58 01/08/2008 8:46:59 AM converter check - 2 20.7 0.06 0.48 01/08/2008 8:47:29 AM 20.71 0.07 0.49 01/08/2008 8:47:59 AM 20.69 0.06 0.62 01/08/2008 8:48:29 AM 20.74 0.04 0.7 01/08/2008 8:48:59 AM 19.76 7.01 -0.09 01/08/2008 8:49:29 AM 20.7 16.02 -0.24 01/08/2008 8:49:59 AM - ZERO 20.88 18.25 -0.24 01/08/2008 8:50:29 AM - ZERO 20.92 18.39 -0.24 01/08/2008 8:50:59 AM - ZERO 20.92 18.39 -0.24 01/08/2008 8:51:29 AM - ZERO 13.83 14.49 1.91 01/08/2008 8:51:59 AM - ZERO 0.37 0.91 3.92 01/08/2008 8:52:29 AM - ZERO 0.04 0.06 4.1 01/08/2008 8:52:59 AM - ZERO 0.03 0.04 4.06 01/08/2008 8:53:29 AM - ZERO 0.04 0.03 4.11



### Page 5 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 8:53:59 AM - ZERO 0.02 0.02 4.06 01/08/2008 8:54:29 AM - ZERO 0.03 0.02 4.09 01/08/2008 8:54:59 AM - ZERO 4.47 0.03 3.74 01/08/2008 8:55:29 AM - ZERO 0.75 0.11 7.77 01/08/2008 8:55:59 AM - ZERO 0.03 0.01 8.01 01/08/2008 8:56:29 AM - Span 0.03 0.01 7.98 01/08/2008 8:56:59 AM - Span 0.03 0.01 7.96 01/08/2008 8:57:29 AM - Span 0.03 0 8 01/08/2008 8:57:59 AM - Span 0.06 0.07 4.42 01/08/2008 8:58:29 AM - Span 0.02 3.46 -0.04 01/08/2008 8:58:59 AM - Span 0.01 3.64 -0.14 01/08/2008 8:59:29 AM - Span 0.01 3.73 -0.15 01/08/2008 8:59:59 AM - Span 0.01 3.74 -0.14 01/08/2008 9:00:29 AM - Span 0 3.74 -0.14 01/08/2008 9:00:59 AM - Span 0.01 3.75 -0.16 01/08/2008 9:01:29 AM - Span 0.01 3.74 -0.15 01/08/2008 9:01:59 AM - Span 0.01 3.75 -0.16 01/08/2008 9:02:29 AM - Span 0.01 3.74 -0.07 01/08/2008 9:02:59 AM - Span 0.01 3.74 -0.17 01/08/2008 9:03:29 AM - Span 0.01 3.75 -0.15 01/08/2008 9:03:59 AM - Span 0.01 3.75 -0.14 01/08/2008 9:04:29 AM - Span 4.82 5.54 -0.07 01/08/2008 9:04:59 AM - Span 10.39 8.82 -0.02 01/08/2008 9:05:29 AM - Span 10.56 9.39 -0.03 01/08/2008 9:05:59 AM - Span 10.57 9.41 -0.01 01/08/2008 9:06:29 AM - Span 10.55 9.43 -0.05 01/08/2008 9:06:59 AM - Span 13.73 8.15 0.19 01/08/2008 9:07:29 AM - Span 20.96 0.17 0.6 01/08/2008 9:07:59 AM - Span 20.97 0.07 0.83 01/08/2008 9:08:29 AM - Span 20.93 0.06 0.85 01/08/2008 9:08:59 AM - Span 20.86 0.06 0.91 01/08/2008 9:09:29 AM - Span 17.49 1.45 0.28 01/08/2008 9:09:59 AM - Span 10.68 8.89 0 01/08/2008 9:10:29 AM - Span 10.52 9.37 -0.02 01/08/2008 9:10:59 AM - Span 10.53 9.39 -0.02 01/08/2008 9:11:29 AM - Span 10.53 9.4 0.04 01/08/2008 9:11:59 AM - Span 19.7 2.35 0.63 01/08/2008 9:12:29 AM - Span 17.81 0.31 0.25 01/08/2008 9:12:59 AM - Span 0.08 3.7 -0.11 01/08/2008 9:13:29 AM - Span 0.02 3.74 -0.1



### Page 6 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 9:13:59 AM - Span 0.02 3.76 -0.06 01/08/2008 9:14:29 AM - Span 17.33 1.13 0.91 01/08/2008 9:14:59 AM - Span 20.87 0.07 1.12 01/08/2008 9:15:29 AM - Span 20.85 0.06 0.7 01/08/2008 9:15:59 AM - Span 18.19 0.55 0.38 01/08/2008 9:16:29 AM - Span 20.87 0.08 0.3 01/08/2008 9:16:59 AM - Span 20.93 0.06 0.26 01/08/2008 9:17:29 AM - Span 20.96 0.04 0.27 01/08/2008 9:17:59 AM - Span 14.43 4.23 0.03 01/08/2008 9:18:29 AM - Span 10.63 9.16 -0.01 01/08/2008 9:18:59 AM - ZERO 10.59 9.35 -0.01 01/08/2008 9:19:29 AM - ZERO 10.57 9.37 -0.02 01/08/2008 9:19:59 AM - Span 10.57 9.38 -0.01 01/08/2008 9:20:29 AM - Span 10.56 9.39 0.58 01/08/2008 9:20:59 AM - Span 1.69 2.7 7.06 01/08/2008 9:21:29 AM - Span 0.07 0.08 7.97 01/08/2008 9:21:59 AM - ZERO 0.05 0.04 7.99 01/08/2008 9:22:29 AM - ZERO 0.05 0.03 7.99 01/08/2008 9:22:59 AM - Span 0.05 0.03 7.99 01/08/2008 9:23:29 AM - Span 0.04 0.02 8.01 01/08/2008 9:23:59 AM - Span 0.04 0.02 7.43 01/08/2008 9:24:29 AM - Span 17.89 0.07 1.18 01/08/2008 9:24:59 AM - Span 20.92 0.07 0.29 01/08/2008 9:25:29 AM - Span 20.95 0.06 0.29 01/08/2008 9:25:59 AM - Span 20.96 0.06 0.28 01/08/2008 9:26:29 AM - Span 9.03 0.53 0.95 01/08/2008 9:26:59 AM - Span 0.09 3.67 -0.09 01/08/2008 9:27:29 AM - Span 0.05 3.7 -0.1 01/08/2008 9:27:59 AM - Span 0.04 3.73 -0.11 01/08/2008 9:28:29 AM - Span 0.04 3.73 -0.1 01/08/2008 9:28:59 AM - Span 0.02 3.74 -0.1 01/08/2008 9:29:29 AM - Span 0.01 3.74 -0.11 01/08/2008 9:29:59 AM - Span 0.03 3.73 -0.11 01/08/2008 9:30:29 AM - Span 0.02 3.74 -0.12 01/08/2008 9:30:59 AM - Span 0.02 3.73 -0.11 01/08/2008 9:31:29 AM - Span 0.02 3.73 -0.09 01/08/2008 9:31:59 AM - Span 0.03 3.73 -0.11 01/08/2008 9:32:29 AM - Span 0.02 3.73 -0.1 01/08/2008 9:32:59 AM - Span 0.03 3.74 -0.12 01/08/2008 9:33:29 AM - Span 0.02 3.73 -0.1



### Page 7 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 9:33:59 AM - Span 0.03 3.73 -0.12 01/08/2008 9:34:29 AM - Span 0.03 3.74 -0.12 01/08/2008 9:34:59 AM - Span 0.03 3.73 -0.11 01/08/2008 9:35:29 AM - Span 0.02 3.73 -0.12 01/08/2008 9:35:59 AM - Span 0.02 3.74 -0.1 01/08/2008 9:36:29 AM - Span 0.17 3.74 -0.04 01/08/2008 9:36:59 AM - Span 20.31 0.33 0.27 01/08/2008 9:37:29 AM - Span 20.92 0.08 0.29 01/08/2008 9:37:59 AM - Span 20.94 0.07 0.3 01/08/2008 9:38:29 AM - Span 20.94 0.06 0.3 01/08/2008 9:38:59 AM - Span 20.95 0.06 0.3 01/08/2008 9:39:29 AM - Span 20.96 0.05 0.31 01/08/2008 9:39:59 AM - Span 20.95 0.06 0.3 01/08/2008 9:40:29 AM - Span 20.95 0.05 0.29 01/08/2008 9:40:59 AM - Span 20.95 0.05 0.29 01/08/2008 9:41:29 AM - Span 20.96 0.04 0.31 01/08/2008 9:41:59 AM - Span 20.97 0.05 0.29 01/08/2008 9:42:29 AM - Span 20.97 0.04 0.3 01/08/2008 9:42:59 AM - Span 20.97 0.05 0.28 01/08/2008 9:43:29 AM - Span 20.96 0.04 0.28 01/08/2008 9:43:59 AM - Span 20.96 0.04 0.3 01/08/2008 9:44:29 AM - Span 20.96 0.04 0.31 01/08/2008 9:44:59 AM - Span 20.97 0.05 0.32 01/08/2008 9:45:29 AM - Span 20.97 0.05 0.29 01/08/2008 9:45:59 AM - Span 20.98 0.05 0.3 01/08/2008 9:46:29 AM - Span 20.98 0.05 0.3 01/08/2008 9:46:59 AM - Span 20.97 0.04 0.3 01/08/2008 9:47:29 AM - Span 20.96 0.05 0.34 01/08/2008 9:47:59 AM - Span 20.98 0.05 0.31 01/08/2008 9:48:29 AM - Span 20.97 0.05 0.32 01/08/2008 9:48:59 AM - Span 20.96 0.05 0.3 01/08/2008 9:49:29 AM - Span 20.98 0.04 0.31 01/08/2008 9:49:59 AM - Span 20.98 0.05 0.28 01/08/2008 9:50:29 AM - Span 20.97 0.05 0.29 01/08/2008 9:50:59 AM - Span 20.99 0.05 0.28 01/08/2008 9:51:29 AM - Span 20.99 0.05 0.29 01/08/2008 9:51:59 AM - Span 20.99 0.05 0.31 01/08/2008 9:52:29 AM - Span 20.98 0.05 0.28 01/08/2008 9:52:59 AM - Span 20.98 0.06 0.3 01/08/2008 9:53:29 AM - Span 20.98 0.05 0.28



### Page 8 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 9:53:59 AM - Span 20.99 0.05 0.29 01/08/2008 9:54:29 AM - Span 20.99 0.05 0.29 01/08/2008 9:54:59 AM - Span 20.98 0.04 0.29 01/08/2008 9:55:29 AM - Span 20.98 0.05 0.28 01/08/2008 9:55:59 AM - Span 20.98 0.04 0.28 01/08/2008 9:56:29 AM - Span 20.97 0.05 0.31 01/08/2008 9:56:59 AM - Span 20.99 0.06 0.3 01/08/2008 9:57:29 AM - Span 20.98 0.06 0.29 01/08/2008 9:57:59 AM - Span 20.98 0.05 0.27 01/08/2008 9:58:29 AM - Span 20.98 0.05 0.29 01/08/2008 9:58:59 AM - Span 20.98 0.05 0.32 01/08/2008 9:59:29 AM - Span 20.98 0.05 0.3 01/08/2008 9:59:59 AM - Span 20.98 0.05 0.29 01/08/2008 10:00:29 AM - Span 20.98 0.05 0.28 01/08/2008 10:00:59 AM - Span 20.97 0.05 0.28 01/08/2008 10:01:29 AM - Span 20.98 0.05 0.29 01/08/2008 10:01:59 AM - Span 20.98 0.05 0.28 01/08/2008 10:02:29 AM - Span 20.98 0.05 0.31 01/08/2008 10:02:59 AM - Span 20.98 0.05 0.27 01/08/2008 10:03:29 AM - Span 20.98 0.05 0.3 01/08/2008 10:03:59 AM - Span 20.98 0.05 0.28 01/08/2008 10:04:29 AM - Span 20.97 0.06 0.33 01/08/2008 10:04:59 AM - Span 20.97 0.05 0.29 01/08/2008 10:05:29 AM - Span 20.97 0.06 0.29 01/08/2008 10:05:59 AM - Span 20.98 0.06 0.31 01/08/2008 10:06:29 AM - Span 20.97 0.05 0.3 01/08/2008 10:06:59 AM - Span 20.97 0.04 0.31 01/08/2008 10:07:29 AM - Span 20.98 0.05 0.28 01/08/2008 10:07:59 AM - Span 20.97 0.06 0.31 01/08/2008 10:08:29 AM - Span 20.96 0.06 0.28 01/08/2008 10:08:59 AM - Span 20.98 0.05 0.29 01/08/2008 10:09:29 AM - Span 20.98 0.05 0.31 01/08/2008 10:09:59 AM - Span 20.97 0.05 0.3 01/08/2008 10:10:29 AM - Span 20.97 0.06 0.32 01/08/2008 10:10:59 AM - Span 20.96 0.06 0.3 01/08/2008 10:11:29 AM - Span 20.97 0.05 0.3 01/08/2008 10:11:59 AM - Span 20.98 0.05 0.33 01/08/2008 10:12:29 AM - Span 20.98 0.05 0.3 01/08/2008 10:12:59 AM - Span 20.99 0.06 0.3 01/08/2008 10:13:29 AM - Span 20.98 0.05 0.32



### Page 9 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 10:13:59 AM - Span 20.99 0.05 0.31 01/08/2008 10:14:29 AM - Span 20.99 0.04 0.27 01/08/2008 10:14:59 AM - Span 20.99 0.04 0.32 01/08/2008 10:15:29 AM - Span 20.98 0.04 0.29 01/08/2008 10:15:59 AM - Span 20.98 0.05 0.3 01/08/2008 10:16:29 AM - Span 20.99 0.04 0.32 01/08/2008 10:16:59 AM - Span 20.99 0.05 0.3 01/08/2008 10:17:29 AM - Span 20.98 0.04 0.32 01/08/2008 10:17:59 AM - Span 20.99 0.05 0.29 01/08/2008 10:18:29 AM - Span 20.98 0.05 0.32 01/08/2008 10:18:59 AM - Span 20.98 0.05 0.32 01/08/2008 10:19:29 AM - Span 20.99 0.05 0.28 01/08/2008 10:19:59 AM - Span 20.98 0.04 0.31 01/08/2008 10:20:29 AM - Span 20.98 0.05 0.29 01/08/2008 10:20:59 AM - Span 20.99 0.04 0.3 01/08/2008 10:21:29 AM - Span 20.99 0.04 0.29 01/08/2008 10:21:59 AM - Span 20.98 0.05 0.31 01/08/2008 10:22:29 AM - Span 20.98 0.04 0.31 01/08/2008 10:22:59 AM - Span 20.99 0.05 0.31 01/08/2008 10:23:29 AM - Span 20.98 0.05 0.31 01/08/2008 10:23:59 AM - Span 20.98 0.04 0.3 01/08/2008 10:24:29 AM - Span 20.99 0.05 0.31 01/08/2008 10:24:59 AM - Span 20.99 0.05 0.29 01/08/2008 10:25:29 AM - Span 20.98 0.05 0.32 01/08/2008 10:25:59 AM - Span 20.98 0.06 0.35 01/08/2008 10:26:29 AM - Span 20.97 0.06 0.32 01/08/2008 10:26:59 AM - Span 20.97 0.05 0.32 01/08/2008 10:27:29 AM - Span 20.97 0.04 0.3 01/08/2008 10:27:59 AM - Span 20.97 0.06 0.33 01/08/2008 10:28:29 AM - Span 20.98 0.06 0.3 01/08/2008 10:28:59 AM - Span 20.97 0.04 0.29 01/08/2008 10:29:29 AM - Span 20.98 0.04 0.34 01/08/2008 10:29:59 AM - Span 20.98 0.05 0.29 01/08/2008 10:30:29 AM - Span 20.98 0.04 0.31 01/08/2008 10:30:59 AM - Span 20.95 0.06 0.39 01/08/2008 10:31:29 AM - Span 20.97 0.05 0.31 01/08/2008 10:31:59 AM - Span 20.98 0.05 0.32 01/08/2008 10:32:29 AM - Span 20.98 0.05 0.31 01/08/2008 10:32:59 AM - Span 20.97 0.05 0.3 01/08/2008 10:33:29 AM - Span 20.98 0.05 0.29



### Page 10 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 10:33:59 AM - Span 20.97 0.05 0.32 01/08/2008 10:34:29 AM - Span 20.99 0.05 0.31 01/08/2008 10:34:59 AM - Span 20.99 0.04 0.33 01/08/2008 10:35:29 AM - Span 20.98 0.04 0.33 01/08/2008 10:35:59 AM - Span 20.98 0.05 0.32 01/08/2008 10:36:29 AM - Span 20.99 0.04 0.31 01/08/2008 10:36:59 AM - Span 20.97 0.05 0.33 01/08/2008 10:37:29 AM - Span 20.98 0.05 0.33 01/08/2008 10:37:59 AM - Span 20.98 0.04 0.34 01/08/2008 10:38:29 AM - Span 20.97 0.04 0.33 01/08/2008 10:38:59 AM 20.98 0.05 0.32 01/08/2008 10:39:29 AM 20.97 0.03 0.31 01/08/2008 10:39:59 AM 20.99 0.04 0.32 01/08/2008 10:40:29 AM 20.98 0.05 0.3 01/08/2008 10:40:59 AM 19.51 0.44 3.74 01/08/2008 10:41:29 AM 12.02 8.74 6.16 01/08/2008 10:41:59 AM 11.63 9.66 6.16 01/08/2008 10:42:29 AM 11.63 9.66 6.15 01/08/2008 10:42:59 AM 11.63 9.67 6.18 01/08/2008 10:43:29 AM 11.63 9.69 6.15 01/08/2008 10:43:59 AM 11.64 9.69 6.05 01/08/2008 10:44:29 AM 11.64 9.65 6.23 01/08/2008 10:44:59 AM 11.62 9.69 6.16 01/08/2008 10:45:29 AM 11.63 9.67 6.25 01/08/2008 10:45:59 AM 11.63 9.68 6.24 01/08/2008 10:46:29 AM Traverse - 1 11.61 9.69 6.23 01/08/2008 10:46:59 AM Traverse - 1 11.61 9.7 6.26 01/08/2008 10:47:29 AM Traverse - 1 11.61 9.69 6.26 01/08/2008 10:47:59 AM Traverse - 1 11.59 9.68 6.32 01/08/2008 10:48:29 AM Traverse - 1 11.61 9.69 6.25 01/08/2008 10:48:59 AM Traverse - 1 11.6 9.7 6.32 01/08/2008 10:49:29 AM Traverse - 1 11.59 9.69 6.32 01/08/2008 10:49:59 AM Traverse - 1 11.61 9.7 6.46 01/08/2008 10:50:29 AM Traverse - 1 11.52 9.69 6.93 01/08/2008 10:50:59 AM Traverse - 1 11.51 9.73 6.67 01/08/2008 10:51:29 AM Traverse - 1 11.56 9.69 6.5 01/08/2008 10:51:59 AM Traverse - 1 11.6 9.69 6.38 01/08/2008 10:52:29 AM Traverse - 1 11.59 9.71 6.36 01/08/2008 10:52:59 AM Traverse - 1 11.6 9.71 6.31 01/08/2008 10:53:29 AM Traverse - 1 11.61 9.69 6.37



### Page 11 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 10:53:59 AM Traverse - 1 11.61 9.7 6.24 01/08/2008 10:54:29 AM Traverse - 1 11.62 9.69 6.25 01/08/2008 10:54:59 AM Traverse - 1 11.61 9.7 6.13 01/08/2008 10:55:29 AM Traverse - 1 11.62 9.74 6.05 01/08/2008 10:55:59 AM Traverse - 1 11.61 9.7 6.3 01/08/2008 10:56:29 AM Traverse - 1 11.6 9.7 6.15 01/08/2008 10:56:59 AM Traverse - 1 11.61 9.7 6.31 01/08/2008 10:57:29 AM Traverse - 1 11.59 9.72 6.29 01/08/2008 10:57:59 AM Traverse - 1 11.59 9.7 6.45 01/08/2008 10:58:29 AM Traverse - 1 11.57 9.72 6.39 01/08/2008 10:58:59 AM Traverse - 1 11.57 9.71 6.45 01/08/2008 10:59:29 AM Traverse - 1 11.59 9.69 6.29 01/08/2008 10:59:59 AM Traverse - 1 11.62 9.69 6.09 01/08/2008 11:00:29 AM Traverse - 1 11.61 9.7 6.26 01/08/2008 11:00:59 AM Traverse - 1 11.61 9.69 6.3 01/08/2008 11:01:29 AM Traverse - 1 11.61 9.69 6.27 01/08/2008 11:01:59 AM Traverse - 1 11.59 9.69 6.29 01/08/2008 11:02:29 AM Traverse - 1 11.59 9.68 6.43 01/08/2008 11:02:59 AM Traverse - 1 11.57 9.69 6.51 01/08/2008 11:03:29 AM Traverse - 1 11.57 9.68 6.54 01/08/2008 11:03:59 AM Traverse - 1 11.57 9.69 6.59 01/08/2008 11:04:29 AM Traverse - 1 11.56 9.67 6.52 01/08/2008 11:04:59 AM Traverse - 1 11.56 9.68 6.58 01/08/2008 11:05:29 AM Run Paused 11.5 9.69 6.92 01/08/2008 11:05:59 AM Run Paused 11.49 9.7 6.85 01/08/2008 11:06:29 AM Run Paused 13.9 8.79 2.19 01/08/2008 11:06:59 AM Run Paused 20.89 0.29 0.35 01/08/2008 11:07:29 AM Run Paused 20.94 0.14 0.37 01/08/2008 11:07:59 AM Run Paused 20.95 0.1 0.41 01/08/2008 11:08:29 AM Run Paused 20.95 0.11 0.42 01/08/2008 11:08:59 AM Run Paused 18.79 0.99 4.32 01/08/2008 11:09:29 AM Run Paused 11.84 8.92 6.69 01/08/2008 11:09:59 AM Run Paused 11.57 9.63 6.73 01/08/2008 11:10:29 AM Run Paused 11.56 9.66 6.81 01/08/2008 11:10:59 AM Run Paused 11.54 9.69 6.87 01/08/2008 11:11:29 AM Run Paused 11.53 9.68 6.73 01/08/2008 11:11:59 AM Run Paused 11.54 9.67 6.77 01/08/2008 11:12:29 AM Run Paused 11.54 9.66 7.08 01/08/2008 11:12:59 AM Run Paused 11.5 9.7 7.07 01/08/2008 11:13:29 AM Traverse - 1 11.52 9.7 7



### Page 12 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 11:13:59 AM Traverse - 1 11.53 9.69 6.83 01/08/2008 11:14:29 AM Traverse - 1 11.53 9.7 6.87 01/08/2008 11:14:59 AM Traverse - 1 11.52 9.69 6.94 01/08/2008 11:15:29 AM Traverse - 1 11.47 9.71 7.25 01/08/2008 11:15:59 AM Traverse - 1 11.45 9.7 7.21 01/08/2008 11:16:29 AM Traverse - 1 11.51 9.69 6.94 01/08/2008 11:16:59 AM Traverse - 1 11.55 9.7 6.74 01/08/2008 11:17:29 AM Traverse - 1 11.56 9.7 6.59 01/08/2008 11:17:59 AM Traverse - 1 11.56 9.69 6.53 01/08/2008 11:18:29 AM Traverse - 1 11.58 9.69 6.54 01/08/2008 11:18:59 AM Traverse - 1 11.57 9.69 6.57 01/08/2008 11:19:29 AM Traverse - 1 11.58 9.67 6.55 01/08/2008 11:19:59 AM Traverse - 1 11.57 9.66 6.49 01/08/2008 11:20:29 AM Traverse - 1 11.57 9.67 6.47 01/08/2008 11:20:59 AM Traverse - 1 11.56 9.7 6.51 01/08/2008 11:21:29 AM Traverse - 1 11.57 9.71 6.43 01/08/2008 11:21:59 AM Traverse - 1 11.55 9.71 6.38 01/08/2008 11:22:29 AM Traverse - 1 11.58 9.71 6.38 01/08/2008 11:22:59 AM Traverse - 1 11.57 9.7 6.48 01/08/2008 11:23:29 AM Traverse - 1 11.56 9.71 6.42 01/08/2008 11:23:59 AM Traverse - 1 11.56 9.7 6.49 01/08/2008 11:24:29 AM Traverse - 1 11.57 9.7 6.48 01/08/2008 11:24:59 AM Traverse - 1 11.57 9.71 6.31 01/08/2008 11:25:29 AM Traverse - 1 11.57 9.7 6.31 01/08/2008 11:25:59 AM Traverse - 1 11.6 9.7 6.25 01/08/2008 11:26:29 AM Traverse - 1 11.59 9.7 6.32 01/08/2008 11:26:59 AM Traverse - 1 11.59 9.68 6.42 01/08/2008 11:27:29 AM Traverse - 1 11.57 9.67 6.43 01/08/2008 11:27:59 AM Traverse - 1 11.59 9.7 6.3 01/08/2008 11:28:29 AM Traverse - 1 11.59 9.68 6.37 01/08/2008 11:28:59 AM Traverse - 1 11.57 9.68 6.35 01/08/2008 11:29:29 AM Traverse - 1 11.53 9.71 5.71 01/08/2008 11:29:59 AM Traverse - 1 11.53 9.69 6.61 01/08/2008 11:30:29 AM Traverse - 1 11.48 9.7 7.02 01/08/2008 11:30:59 AM Traverse - 1 11.47 9.71 6.66 01/08/2008 11:31:29 AM Traverse - 1 11.54 9.7 6.49 01/08/2008 11:31:59 AM Run Paused 11.55 9.69 6.47 01/08/2008 11:32:29 AM Run Paused 11.55 9.68 6.51 01/08/2008 11:32:59 AM Run Paused 11.54 9.67 6.64 01/08/2008 11:33:29 AM Run Paused 11.55 9.68 6.58



### Page 13 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 11:33:59 AM Run Paused 16.06 6.95 2.01 01/08/2008 11:34:29 AM Run Paused 18.02 1.92 4.42 01/08/2008 11:34:59 AM Run Paused 11.77 9.12 6.48 01/08/2008 11:35:29 AM Run Paused 11.57 9.66 6.47 01/08/2008 11:35:59 AM Run Paused 11.57 9.66 6.56 01/08/2008 11:36:29 AM Run Paused 11.58 9.68 6.57 01/08/2008 11:36:59 AM Run Paused 11.58 9.71 6.41 01/08/2008 11:37:29 AM Traverse - 1 11.58 9.68 6.34 01/08/2008 11:37:59 AM Traverse - 1 11.58 9.69 6.39 01/08/2008 11:38:29 AM Traverse - 1 11.6 9.69 6.28 01/08/2008 11:38:59 AM Traverse - 1 11.59 9.7 6.34 01/08/2008 11:39:29 AM Traverse - 1 11.59 9.68 6.39 01/08/2008 11:39:59 AM Traverse - 1 11.59 9.7 6.36 01/08/2008 11:40:29 AM Traverse - 1 11.57 9.7 6.41 01/08/2008 11:40:59 AM Traverse - 1 11.58 9.69 6.45 01/08/2008 11:41:29 AM Traverse - 1 11.58 9.7 6.47 01/08/2008 11:41:59 AM Traverse - 1 11.58 9.7 6.49 01/08/2008 11:42:29 AM Traverse - 1 11.57 9.68 6.56 01/08/2008 11:42:59 AM Traverse - 1 11.6 9.69 6.35 01/08/2008 11:43:29 AM Traverse - 1 11.59 9.67 6.45 01/08/2008 11:43:59 AM Traverse - 1 11.57 9.69 6.45 01/08/2008 11:44:29 AM Traverse - 1 11.57 9.7 6.36 01/08/2008 11:44:59 AM Traverse - 1 11.59 9.69 6.33 01/08/2008 11:45:29 AM Traverse - 1 11.53 9.66 6.87 01/08/2008 11:45:59 AM Traverse - 1 11.51 9.71 6.95 01/08/2008 11:46:29 AM Traverse - 1 11.54 9.71 6.57 01/08/2008 11:46:59 AM Traverse - 1 11.56 9.68 6.52 01/08/2008 11:47:29 AM Traverse - 1 11.57 9.68 6.46 01/08/2008 11:47:59 AM Traverse - 1 11.58 9.7 6.4 01/08/2008 11:48:29 AM Traverse - 1 11.6 9.69 6.32 01/08/2008 11:48:59 AM Traverse - 1 11.57 9.7 6.38 01/08/2008 11:49:29 AM Traverse - 1 11.59 9.69 6.33 01/08/2008 11:49:59 AM Traverse - 1 11.57 9.69 6.41 01/08/2008 11:50:29 AM Traverse - 1 11.57 9.68 6.5 01/08/2008 11:50:59 AM Traverse - 1 11.55 9.69 6.57 01/08/2008 11:51:29 AM Traverse - 1 11.58 9.7 6.52 01/08/2008 11:51:59 AM Traverse - 1 11.58 9.72 6.32 01/08/2008 11:52:29 AM Traverse - 1 11.6 9.72 6.32 01/08/2008 11:52:59 AM Traverse - 1 11.58 9.71 6.44 01/08/2008 11:53:29 AM Traverse - 1 11.6 9.71 6.33



### Page 14 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 11:53:59 AM Traverse - 1 11.6 9.72 6.39 01/08/2008 11:54:29 AM Traverse - 1 11.6 9.74 6.24 01/08/2008 11:54:59 AM Traverse - 1 11.6 9.72 6.43 01/08/2008 11:55:29 AM Traverse - 1 11.53 9.72 6.84 01/08/2008 11:55:59 AM Traverse - 1 11.51 9.74 6.77 01/08/2008 11:56:29 AM Run Paused 11.56 9.74 6.5 01/08/2008 11:56:59 AM Run Paused 11.59 9.73 6.41 01/08/2008 11:57:29 AM Run Paused 11.6 9.73 6.5 01/08/2008 11:57:59 AM Run Paused 12.02 9.69 3.55 01/08/2008 11:58:29 AM Run Paused 19.81 0.69 3.17 01/08/2008 11:58:59 AM Run Paused 12.04 8.73 6.18 01/08/2008 11:59:29 AM Run Paused 11.61 9.68 6.46 01/08/2008 11:59:59 AM Run Paused 11.6 9.7 6.37 01/08/2008 12:00:29 PM Run Paused 11.6 9.69 6.46 01/08/2008 12:00:59 PM Run Paused 11.57 9.71 6.58 01/08/2008 12:01:29 PM Traverse - 1 11.58 9.7 6.59 01/08/2008 12:01:59 PM Traverse - 1 11.58 9.69 6.53 01/08/2008 12:02:29 PM Traverse - 1 11.58 9.72 6.43 01/08/2008 12:02:59 PM Traverse - 1 11.58 9.7 6.55 01/08/2008 12:03:29 PM Traverse - 1 11.6 9.7 6.44 01/08/2008 12:03:59 PM Traverse - 1 11.59 9.73 6.35 01/08/2008 12:04:29 PM Traverse - 1 11.59 9.71 6.38 01/08/2008 12:04:59 PM Traverse - 1 11.6 9.69 6.31 01/08/2008 12:05:29 PM Traverse - 1 11.59 9.7 6.37 01/08/2008 12:05:59 PM Traverse - 1 11.59 9.72 6.42 01/08/2008 12:06:29 PM Traverse - 1 11.59 9.7 6.5 01/08/2008 12:06:59 PM Traverse - 1 11.59 9.72 6.34 01/08/2008 12:07:29 PM Traverse - 1 11.58 9.69 6.52 01/08/2008 12:07:59 PM Traverse - 1 11.57 9.69 6.48 01/08/2008 12:08:29 PM Traverse - 1 11.6 9.69 6.44 01/08/2008 12:08:59 PM Traverse - 1 11.58 9.68 6.55 01/08/2008 12:09:29 PM Traverse - 1 11.59 9.7 6.47 01/08/2008 12:09:59 PM Traverse - 1 11.57 9.68 6.58 01/08/2008 12:10:29 PM Traverse - 1 11.51 9.69 6.82 01/08/2008 12:10:59 PM Traverse - 1 11.53 9.72 6.56 01/08/2008 12:11:29 PM Traverse - 1 11.56 9.7 6.47 01/08/2008 12:11:59 PM Traverse - 1 11.59 9.7 6.34 01/08/2008 12:12:29 PM Traverse - 1 11.6 9.69 6.29 01/08/2008 12:12:59 PM Traverse - 1 11.59 9.69 6.3 01/08/2008 12:13:29 PM Traverse - 1 11.6 9.7 6.28



### Page 15 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 12:13:59 PM Traverse - 1 11.57 9.68 6.44 01/08/2008 12:14:29 PM Traverse - 1 11.6 9.66 6.42 01/08/2008 12:14:59 PM Traverse - 1 11.61 9.68 6.4 01/08/2008 12:15:29 PM Traverse - 1 11.59 9.69 6.4 01/08/2008 12:15:59 PM Traverse - 1 11.57 9.72 6.5 01/08/2008 12:16:29 PM Traverse - 1 11.58 9.68 6.55 01/08/2008 12:16:59 PM Traverse - 1 11.59 9.69 6.32 01/08/2008 12:17:29 PM Traverse - 1 11.61 9.67 6.34 01/08/2008 12:17:59 PM Traverse - 1 11.6 9.71 6.26 01/08/2008 12:18:29 PM Traverse - 1 11.62 9.67 6.2 01/08/2008 12:18:59 PM Traverse - 1 11.59 9.71 6.22 01/08/2008 12:19:29 PM Traverse - 1 11.59 9.68 6.4 01/08/2008 12:19:59 PM Traverse - 1 11.58 9.68 6.65 01/08/2008 12:20:29 PM 11.56 9.7 6.67 01/08/2008 12:20:59 PM 11.56 9.69 5.29 01/08/2008 12:21:29 PM 10.12 8.5 0.29 01/08/2008 12:21:59 PM 10.56 9.39 0.03 01/08/2008 12:22:29 PM 10.56 9.41 0.03 01/08/2008 12:22:59 PM - ZERO 10.56 9.41 0.03 01/08/2008 12:23:29 PM - ZERO 10.56 9.4 0.02 01/08/2008 12:23:59 PM - ZERO 10.57 9.41 0.05 01/08/2008 12:24:29 PM - ZERO 10.56 9.4 0.02 01/08/2008 12:24:59 PM - ZERO 10.56 9.4 0.04 01/08/2008 12:25:29 PM - ZERO 8.01 8.43 4.42 01/08/2008 12:25:59 PM - ZERO 0.17 0.34 7.91 01/08/2008 12:26:29 PM - Span 0.09 0.1 8 01/08/2008 12:26:59 PM - ZERO 0.07 0.07 7.99 01/08/2008 12:27:29 PM - ZERO 0.08 0.06 7.16 01/08/2008 12:27:59 PM - ZERO 0.06 2.71 0.52 01/08/2008 12:28:29 PM - ZERO 0.04 3.73 -0.04 01/08/2008 12:28:59 PM - ZERO 0.05 3.75 -0.07 01/08/2008 12:29:29 PM - Span 0.05 3.76 -0.05 01/08/2008 12:29:59 PM - Span 0.05 3.76 -0.07 01/08/2008 12:30:29 PM - Span 0.05 3.75 -0.06 01/08/2008 12:30:59 PM - Span 0.04 3.75 -0.08 01/08/2008 12:31:29 PM - Span 0.04 3.75 -0.08 01/08/2008 12:31:59 PM - Span 0.04 3.75 -0.09 01/08/2008 12:32:29 PM - Span 0.04 3.74 -0.1 01/08/2008 12:32:59 PM - Span 0.04 3.75 -0.11 01/08/2008 12:33:29 PM - Span 0.04 3.75 -0.11



### Page 16 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 12:33:59 PM - Span 0.05 3.74 -0.09 01/08/2008 12:34:29 PM - Span 0.04 3.74 0.47 01/08/2008 12:34:59 PM - Span 9.12 7.84 5.87 01/08/2008 12:35:29 PM - Span 11.43 9.61 7.01 01/08/2008 12:35:59 PM - Span 11.45 9.68 6.89 01/08/2008 12:36:29 PM - Span 11.5 9.65 6.62 01/08/2008 12:36:59 PM - Span 11.54 9.65 6.5 01/08/2008 12:37:29 PM - Span 11.56 9.66 6.48 01/08/2008 12:37:59 PM - Span 11.57 9.65 6.37 01/08/2008 12:38:29 PM - Span 11.58 9.66 6.41 01/08/2008 12:38:59 PM - Span 11.58 9.69 6.34 01/08/2008 12:39:29 PM - Span 11.59 9.68 6.42 01/08/2008 12:39:59 PM Run 2 - 1 11.58 9.66 6.45 01/08/2008 12:40:29 PM Run 2 - 1 11.58 9.67 6.41 01/08/2008 12:40:59 PM Run 2 - 1 11.56 9.69 6.52 01/08/2008 12:41:29 PM Run 2 - 1 11.56 9.66 6.46 01/08/2008 12:41:59 PM Run 2 - 1 11.56 9.67 6.45 01/08/2008 12:42:29 PM Run 2 - 1 11.56 9.66 6.51 01/08/2008 12:42:59 PM Run 2 - 1 11.59 9.67 6.38 01/08/2008 12:43:29 PM Run 2 - 1 11.58 9.68 6.39 01/08/2008 12:43:59 PM Run 2 - 1 11.59 9.7 6.32 01/08/2008 12:44:29 PM Run 2 - 1 11.61 9.68 6.15 01/08/2008 12:44:59 PM Run 2 - 1 11.59 9.67 6.27 01/08/2008 12:45:29 PM Run 2 - 1 11.61 9.69 6.27 01/08/2008 12:45:59 PM Run 2 - 1 11.59 9.69 6.33 01/08/2008 12:46:29 PM Run 2 - 1 11.59 9.7 6.27 01/08/2008 12:46:59 PM Run 2 - 1 11.58 9.67 6.38 01/08/2008 12:47:29 PM Run 2 - 1 11.57 9.69 6.43 01/08/2008 12:47:59 PM Run 2 - 1 11.58 9.67 6.5 01/08/2008 12:48:29 PM Run 2 - 1 11.59 9.66 6.42 01/08/2008 12:48:59 PM Run 2 - 1 11.59 9.69 6.44 01/08/2008 12:49:29 PM Run 2 - 1 11.58 9.69 6.38 01/08/2008 12:49:59 PM Run 2 - 1 11.59 9.68 6.4 01/08/2008 12:50:29 PM Run 2 - 1 11.53 9.7 6.79 01/08/2008 12:50:59 PM Run 2 - 1 11.52 9.69 6.75 01/08/2008 12:51:29 PM Run 2 - 1 11.58 9.71 6.38 01/08/2008 12:51:59 PM Run 2 - 1 11.59 9.72 6.31 01/08/2008 12:52:29 PM Run 2 - 1 11.62 9.68 6.16 01/08/2008 12:52:59 PM Run 2 - 1 11.6 9.69 6.32 01/08/2008 12:53:29 PM Run 2 - 1 11.59 9.7 6.34



### Page 17 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 12:53:59 PM Run 2 - 1 11.58 9.68 6.39 01/08/2008 12:54:29 PM Run 2 - 1 11.59 9.67 6.39 01/08/2008 12:54:59 PM Run 2 - 1 11.59 9.67 6.15 01/08/2008 12:55:29 PM Run 2 - 1 11.59 9.66 6.29 01/08/2008 12:55:59 PM Run 2 - 1 11.59 9.69 6.29 01/08/2008 12:56:29 PM Run 2 - 1 11.6 9.66 6.19 01/08/2008 12:56:59 PM Run 2 - 1 11.61 9.66 6.23 01/08/2008 12:57:29 PM Run 2 - 1 11.62 9.64 6.19 01/08/2008 12:57:59 PM Run 2 - 1 11.6 9.68 6.13 01/08/2008 12:58:29 PM Run 2 - 1 11.61 9.63 6.16 01/08/2008 12:58:59 PM Run 2 - 1 11.61 9.64 6.33 01/08/2008 12:59:29 PM Run 2 - 1 11.61 9.66 6.3 01/08/2008 12:59:59 PM Run 2 - 1 11.61 9.64 6.22 01/08/2008 1:00:29 PM Run 2 - 1 11.63 9.67 6.09 01/08/2008 1:00:59 PM 11.62 9.65 6.2 01/08/2008 1:01:29 PM 11.61 9.67 5.54 01/08/2008 1:01:59 PM 1.56 5.12 0.42 01/08/2008 1:02:29 PM 0.1 3.77 -0.17 01/08/2008 1:02:59 PM - Span 0.08 3.76 -0.14 01/08/2008 1:03:29 PM - ZERO 0.08 3.75 -0.15 01/08/2008 1:03:59 PM - ZERO 0.06 3.75 -0.16 01/08/2008 1:04:29 PM - ZERO 4.2 5.14 -0.08 01/08/2008 1:04:59 PM - ZERO 10.36 9.04 -0.06 01/08/2008 1:05:29 PM - Span 10.54 9.34 -0.02 01/08/2008 1:05:59 PM - ZERO 10.54 9.35 -0.04 01/08/2008 1:06:29 PM - ZERO 10.55 9.35 -0.03 01/08/2008 1:06:59 PM - ZERO 7.58 8.09 4.02 01/08/2008 1:07:29 PM - ZERO 0.17 0.31 7.83 01/08/2008 1:07:59 PM - ZERO 0.09 0.07 7.92 01/08/2008 1:08:29 PM - ZERO 0.07 0.05 7.91 01/08/2008 1:08:59 PM - ZERO 0.08 0.03 7.96 01/08/2008 1:09:29 PM - ZERO 5.59 3.93 6.64 01/08/2008 1:09:59 PM - ZERO 9.66 8.03 0.83 01/08/2008 1:10:29 PM - ZERO 11.39 8.16 -0.02 01/08/2008 1:10:59 PM - ZERO 10.55 9.33 -0.09 01/08/2008 1:11:29 PM - ZERO 10.54 9.35 -0.07 01/08/2008 1:11:59 PM - ZERO 10.7 9.36 2.98 01/08/2008 1:12:29 PM - ZERO 11.63 9.62 5.8 01/08/2008 1:12:59 PM - ZERO 11.6 9.61 6.1 01/08/2008 1:13:29 PM - ZERO 11.62 9.64 6.14



### Page 18 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 1:13:59 PM - ZERO 11.64 9.64 6.04 01/08/2008 1:14:29 PM run 3 - 1 11.63 9.65 6.2 01/08/2008 1:14:59 PM run 3 - 1 11.64 9.69 6.04 01/08/2008 1:15:29 PM run 3 - 1 11.64 9.67 5.94 01/08/2008 1:15:59 PM run 3 - 1 11.6 9.66 6.31 01/08/2008 1:16:29 PM run 3 - 1 11.58 9.67 6.29 01/08/2008 1:16:59 PM run 3 - 1 11.61 9.66 6.14 01/08/2008 1:17:29 PM run 3 - 1 11.66 9.66 6 01/08/2008 1:17:59 PM run 3 - 1 11.65 9.65 6.03 01/08/2008 1:18:29 PM run 3 - 1 11.62 9.65 6.24 01/08/2008 1:18:59 PM run 3 - 1 11.63 9.63 6.08 01/08/2008 1:19:29 PM run 3 - 1 11.63 9.66 6.05 01/08/2008 1:19:59 PM run 3 - 1 11.64 9.63 6.05 01/08/2008 1:20:29 PM run 3 - 1 11.63 9.64 6.06 01/08/2008 1:20:59 PM run 3 - 1 11.64 9.63 6.04 01/08/2008 1:21:29 PM run 3 - 1 11.63 9.63 6.13 01/08/2008 1:21:59 PM run 3 - 1 11.61 9.65 6.05 01/08/2008 1:22:29 PM run 3 - 1 11.61 9.64 5.99 01/08/2008 1:22:59 PM run 3 - 1 11.61 9.64 5.91 01/08/2008 1:23:29 PM run 3 - 1 11.62 9.62 5.94 01/08/2008 1:23:59 PM run 3 - 1 11.62 9.62 6.18 01/08/2008 1:24:29 PM run 3 - 1 11.57 9.61 6.27 01/08/2008 1:24:59 PM run 3 - 1 11.6 9.61 6.29 01/08/2008 1:25:29 PM run 3 - 1 11.59 9.63 6.24 01/08/2008 1:25:59 PM run 3 - 1 11.59 9.61 6.22 01/08/2008 1:26:29 PM run 3 - 1 11.58 9.61 6.26 01/08/2008 1:26:59 PM run 3 - 1 11.57 9.62 6.22 01/08/2008 1:27:29 PM run 3 - 1 11.61 9.63 6.05 01/08/2008 1:27:59 PM run 3 - 1 11.6 9.64 6.08 01/08/2008 1:28:29 PM run 3 - 1 11.61 9.6 6.08 01/08/2008 1:28:59 PM run 3 - 1 11.61 9.65 6 01/08/2008 1:29:29 PM run 3 - 1 11.61 9.64 6.02 01/08/2008 1:29:59 PM run 3 - 1 11.61 9.65 6 01/08/2008 1:30:29 PM run 3 - 1 11.6 9.63 5.95 01/08/2008 1:30:59 PM run 3 - 1 11.53 9.63 5.69 01/08/2008 1:31:29 PM run 3 - 1 11.51 9.65 6.59 01/08/2008 1:31:59 PM run 3 - 1 11.56 9.63 6.41 01/08/2008 1:32:29 PM run 3 - 1 11.56 9.68 6.46 01/08/2008 1:32:59 PM run 3 - 1 11.57 9.67 6.31 01/08/2008 1:33:29 PM run 3 - 1 11.59 9.68 6.22



### Page 19 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 1:33:59 PM run 3 - 1 11.58 9.69 6.31 01/08/2008 1:34:29 PM run 3 - 1 11.58 9.69 6.28 01/08/2008 1:34:59 PM run 3 - 1 11.59 9.71 6.25 01/08/2008 1:35:29 PM run 3 - 2 11.59 9.7 6.19 01/08/2008 1:35:59 PM 11.59 9.7 6.25 01/08/2008 1:36:29 PM 11.59 9.71 6.14 01/08/2008 1:36:59 PM 10.6 9.56 3.09 01/08/2008 1:37:29 PM 0.29 4.1 -0.09 01/08/2008 1:37:59 PM 0.1 3.84 -0.16 01/08/2008 1:38:29 PM - Span 0.08 3.8 -0.14 01/08/2008 1:38:59 PM - Span 0.07 3.8 -0.15 01/08/2008 1:39:29 PM - Span 0.07 3.79 -0.16 01/08/2008 1:39:59 PM - ZERO 0.08 3.78 -0.17 01/08/2008 1:40:29 PM - ZERO 0.07 3.8 -0.14 01/08/2008 1:40:59 PM - ZERO 0.06 3.78 -0.15 01/08/2008 1:41:29 PM - ZERO 5.44 5.81 -0.09 01/08/2008 1:41:59 PM - ZERO 10.43 9.16 -0.02 01/08/2008 1:42:29 PM - Span 10.51 9.35 -0.03 01/08/2008 1:42:59 PM - ZERO 10.52 9.35 -0.02 01/08/2008 1:43:29 PM - ZERO 10.54 9.38 -0.04 01/08/2008 1:43:59 PM - ZERO 10.53 9.38 -0.02 01/08/2008 1:44:29 PM - ZERO 7.36 7.97 3.88 01/08/2008 1:44:59 PM - ZERO 0.15 0.29 7.81 01/08/2008 1:45:29 PM - Span 0.07 0.1 7.95 01/08/2008 1:45:59 PM - ZERO 0.07 0.07 7.95 01/08/2008 1:46:29 PM - ZERO 7.18 5.49 1.86 01/08/2008 1:46:59 PM - ZERO 10.99 9.26 4.78 01/08/2008 1:47:29 PM - ZERO 11.43 9.44 6.43 01/08/2008 1:47:59 PM - ZERO 11.51 9.61 6.72 01/08/2008 1:48:29 PM - ZERO 11.51 9.63 6.71 01/08/2008 1:48:59 PM run 4 - 1 11.52 9.64 6.65 01/08/2008 1:49:29 PM run 4 - 1 11.52 9.64 6.59 01/08/2008 1:49:59 PM run 4 - 1 11.53 9.64 6.56 01/08/2008 1:50:29 PM run 4 - 1 11.54 9.65 6.52 01/08/2008 1:50:59 PM run 4 - 1 11.54 9.66 6.47 01/08/2008 1:51:29 PM run 4 - 1 11.55 9.65 6.39 01/08/2008 1:51:59 PM run 4 - 1 11.55 9.64 6.38 01/08/2008 1:52:29 PM run 4 - 1 11.55 9.63 6.44 01/08/2008 1:52:59 PM run 4 - 1 11.54 9.64 6.45 01/08/2008 1:53:29 PM run 4 - 1 11.53 9.64 6.42



### Page 20 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 1:53:59 PM run 4 - 1 11.56 9.63 6.35 01/08/2008 1:54:29 PM run 4 - 1 11.57 9.62 6.33 01/08/2008 1:54:59 PM run 4 - 1 11.56 9.62 6.39 01/08/2008 1:55:29 PM run 4 - 1 11.52 9.62 6.68 01/08/2008 1:55:59 PM run 4 - 1 11.47 9.66 6.81 01/08/2008 1:56:29 PM run 4 - 1 11.52 9.66 6.38 01/08/2008 1:56:59 PM run 4 - 1 11.57 9.64 6.22 01/08/2008 1:57:29 PM run 4 - 1 11.57 9.64 6.19 01/08/2008 1:57:59 PM run 4 - 1 11.57 9.65 6.18 01/08/2008 1:58:29 PM run 4 - 1 11.57 9.64 6.27 01/08/2008 1:58:59 PM run 4 - 1 11.57 9.63 6.29 01/08/2008 1:59:29 PM run 4 - 1 11.57 9.64 6.21 01/08/2008 1:59:59 PM run 4 - 1 11.58 9.64 6.11 01/08/2008 2:00:29 PM run 4 - 1 11.55 9.63 6.28 01/08/2008 2:00:59 PM run 4 - 1 11.56 9.61 6.32 01/08/2008 2:01:29 PM run 4 - 1 11.55 9.65 6.35 01/08/2008 2:01:59 PM run 4 - 1 11.56 9.63 6.3 01/08/2008 2:02:29 PM run 4 - 1 11.57 9.64 6.19 01/08/2008 2:02:59 PM run 4 - 1 11.56 9.65 6.22 01/08/2008 2:03:29 PM run 4 - 1 11.58 9.66 6.08 01/08/2008 2:03:59 PM run 4 - 1 11.61 9.65 5.95 01/08/2008 2:04:29 PM run 4 - 1 11.6 9.65 5.98 01/08/2008 2:04:59 PM run 4 - 1 11.59 9.64 6.23 01/08/2008 2:05:29 PM run 4 - 1 11.58 9.65 6.19 01/08/2008 2:05:59 PM run 4 - 1 11.57 9.66 6.2 01/08/2008 2:06:29 PM run 4 - 1 11.55 9.66 6.27 01/08/2008 2:06:59 PM run 4 - 1 11.56 9.65 6.24 01/08/2008 2:07:29 PM run 4 - 1 11.58 9.65 6.12 01/08/2008 2:07:59 PM run 4 - 1 11.58 9.64 6.07 01/08/2008 2:08:29 PM run 4 - 1 11.59 9.64 6.19 01/08/2008 2:08:59 PM run 4 - 1 11.58 9.65 6.1 01/08/2008 2:09:29 PM run 4 - 1 11.59 9.62 6.17 01/08/2008 2:09:59 PM 11.59 9.64 6.16 01/08/2008 2:10:29 PM 8.06 8.25 3.89 01/08/2008 2:10:59 PM 0.11 3.82 -0.14 01/08/2008 2:11:29 PM - ZERO 0.06 3.76 -0.15 01/08/2008 2:11:59 PM - Span 0.05 3.75 -0.15 01/08/2008 2:12:29 PM - Span 0.04 3.76 -0.15 01/08/2008 2:12:59 PM - Span 0.03 3.74 -0.14 01/08/2008 2:13:29 PM - Span 0.04 3.74 0.04



### Page 21 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 2:13:59 PM - ZERO 0.05 0.96 7.16 01/08/2008 2:14:29 PM - ZERO 0.05 0.06 7.92 01/08/2008 2:14:59 PM - ZERO 0.05 0.03 7.92 01/08/2008 2:15:29 PM - ZERO 0.04 0.03 7.91 01/08/2008 2:15:59 PM - ZERO 7.71 5.81 0.67 01/08/2008 2:16:29 PM - Span 10.46 9.17 0 01/08/2008 2:16:59 PM - ZERO 10.5 9.3 -0.03 01/08/2008 2:17:29 PM - ZERO 10.52 9.34 -0.08 01/08/2008 2:17:59 PM - ZERO 10.5 9.35 0.44 01/08/2008 2:18:29 PM - ZERO 11.22 9.49 5.11 01/08/2008 2:18:59 PM - ZERO 11.55 9.61 6.13 01/08/2008 2:19:29 PM - ZERO 11.59 9.62 6.06 01/08/2008 2:19:59 PM RUN5 - 1 11.58 9.63 6.01 01/08/2008 2:20:29 PM RUN5 - 1 11.58 9.63 6 01/08/2008 2:20:59 PM RUN5 - 1 11.59 9.63 5.96 01/08/2008 2:21:29 PM RUN5 - 1 11.57 9.62 6.18 01/08/2008 2:21:59 PM RUN5 - 1 11.58 9.63 6.02 01/08/2008 2:22:29 PM RUN5 - 1 11.59 9.62 6.02 01/08/2008 2:22:59 PM RUN5 - 1 11.59 9.62 6.08 01/08/2008 2:23:29 PM RUN5 - 1 11.58 9.62 6.09 01/08/2008 2:23:59 PM RUN5 - 1 11.58 9.62 6.15 01/08/2008 2:24:29 PM RUN5 - 1 11.57 9.63 6.12 01/08/2008 2:24:59 PM RUN5 - 1 11.58 9.62 6.21 01/08/2008 2:25:29 PM RUN5 - 1 11.55 9.64 6.45 01/08/2008 2:25:59 PM RUN5 - 1 11.51 9.65 6.5 01/08/2008 2:26:29 PM RUN5 - 1 11.53 9.65 6.42 01/08/2008 2:26:59 PM RUN5 - 1 11.55 9.64 6.27 01/08/2008 2:27:29 PM RUN5 - 1 11.55 9.64 6.27 01/08/2008 2:27:59 PM RUN5 - 1 11.56 9.65 6.21 01/08/2008 2:28:29 PM RUN5 - 1 11.57 9.65 6.12 01/08/2008 2:28:59 PM RUN5 - 1 11.58 9.66 6.09 01/08/2008 2:29:29 PM RUN5 - 1 11.57 9.63 6.14 01/08/2008 2:29:59 PM RUN5 - 1 11.57 9.64 6.2 01/08/2008 2:30:29 PM RUN5 - 1 11.58 9.66 5.81 01/08/2008 2:30:59 PM RUN5 - 1 11.55 9.67 5.44 01/08/2008 2:31:29 PM RUN5 - 1 11.53 9.7 6.06 01/08/2008 2:31:59 PM RUN5 - 1 11.57 9.68 6.11 01/08/2008 2:32:29 PM RUN5 - 1 11.55 9.67 6.08 01/08/2008 2:32:59 PM RUN5 - 1 11.58 9.65 6.11 01/08/2008 2:33:29 PM RUN5 - 1 11.56 9.66 6.22



### Page 22 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 2:33:59 PM RUN5 - 1 11.54 9.68 6.37 01/08/2008 2:34:29 PM RUN5 - 1 11.54 9.66 6.46 01/08/2008 2:34:59 PM RUN5 - 1 11.54 9.69 6.26 01/08/2008 2:35:29 PM RUN5 - 1 11.53 9.67 6.72 01/08/2008 2:35:59 PM RUN5 - 1 11.47 9.71 6.66 01/08/2008 2:36:29 PM RUN5 - 1 11.5 9.65 6.45 01/08/2008 2:36:59 PM RUN5 - 1 11.55 9.63 6.25 01/08/2008 2:37:29 PM RUN5 - 1 11.56 9.62 6.19 01/08/2008 2:37:59 PM RUN5 - 1 11.57 9.63 6.08 01/08/2008 2:38:29 PM RUN5 - 1 11.56 9.63 6.24 01/08/2008 2:38:59 PM RUN5 - 1 11.56 9.63 6.18 01/08/2008 2:39:29 PM RUN5 - 1 11.57 9.62 6.12 01/08/2008 2:39:59 PM RUN5 - 1 11.55 9.62 6.17 01/08/2008 2:40:29 PM RUN5 - 1 11.57 9.59 6.27 01/08/2008 2:40:59 PM 11.55 9.63 6.16 01/08/2008 2:41:29 PM 11.53 9.61 4.73 01/08/2008 2:41:59 PM 3.36 6.19 0.08 01/08/2008 2:42:29 PM 0.06 3.77 -0.18 01/08/2008 2:42:59 PM 0.04 3.73 -0.17 01/08/2008 2:43:29 PM - Span 0.03 3.72 -0.17 01/08/2008 2:43:59 PM - Span 0.05 3.7 -0.18 01/08/2008 2:44:29 PM - Span 0.04 3.71 -0.16 01/08/2008 2:44:59 PM - ZERO 0.03 3.72 -0.19 01/08/2008 2:45:29 PM - ZERO 0.04 3.71 -0.12 01/08/2008 2:45:59 PM - ZERO 0.05 2.73 6.54 01/08/2008 2:46:29 PM - ZERO 0.04 0.05 7.9 01/08/2008 2:46:59 PM - Span 0.05 0.03 7.91 01/08/2008 2:47:29 PM - ZERO 0.05 0.01 7.9 01/08/2008 2:47:59 PM - ZERO 0.04 0 7.88 01/08/2008 2:48:29 PM - ZERO 0.03 0.86 1.38 01/08/2008 2:48:59 PM - Span 0.03 3.59 -0.14 01/08/2008 2:49:29 PM - Span 0.03 3.65 -0.19 01/08/2008 2:49:59 PM - Span 0.34 3.66 -0.1 01/08/2008 2:50:29 PM - Span 9.6 8.29 -0.05 01/08/2008 2:50:59 PM - Span 10.5 9.22 -0.05 01/08/2008 2:51:29 PM - ZERO 10.52 9.24 -0.08 01/08/2008 2:51:59 PM - ZERO 10.51 9.28 -0.06 01/08/2008 2:52:29 PM - ZERO 10.51 9.3 -0.08 01/08/2008 2:52:59 PM - ZERO 10.56 9.27 3.58 01/08/2008 2:53:29 PM - ZERO 11.42 9.47 5.96



### Page 23 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 2:53:59 PM - ZERO 11.58 9.53 6.04 01/08/2008 2:54:29 PM - ZERO 11.58 9.53 6.07 01/08/2008 2:54:59 PM - ZERO 11.56 9.55 6.24 01/08/2008 2:55:29 PM - ZERO 11.54 9.53 6.4 01/08/2008 2:55:59 PM RUN6 - 1 11.54 9.52 6.56 01/08/2008 2:56:29 PM RUN6 - 1 11.54 9.53 6.46 01/08/2008 2:56:59 PM RUN6 - 1 11.54 9.55 6.51 01/08/2008 2:57:29 PM RUN6 - 1 11.52 9.57 6.56 01/08/2008 2:57:59 PM RUN6 - 1 11.51 9.55 6.63 01/08/2008 2:58:29 PM RUN6 - 1 11.54 9.53 6.6 01/08/2008 2:58:59 PM RUN6 - 1 11.54 9.52 6.51 01/08/2008 2:59:29 PM RUN6 - 1 11.54 9.56 6.5 01/08/2008 2:59:59 PM RUN6 - 1 11.52 9.54 6.6 01/08/2008 3:00:29 PM RUN6 - 1 11.52 9.59 6.72 01/08/2008 3:00:59 PM RUN6 - 1 11.51 9.52 6.9 01/08/2008 3:01:29 PM RUN6 - 1 11.51 9.56 6.68 01/08/2008 3:01:59 PM RUN6 - 1 11.53 9.54 6.74 01/08/2008 3:02:29 PM RUN6 - 1 11.51 9.57 6.63 01/08/2008 3:02:59 PM RUN6 - 1 11.52 9.58 6.46 01/08/2008 3:03:29 PM RUN6 - 1 11.52 9.55 6.57 01/08/2008 3:03:59 PM RUN6 - 1 11.51 9.56 6.71 01/08/2008 3:04:29 PM RUN6 - 1 11.51 9.59 6.51 01/08/2008 3:04:59 PM RUN6 - 1 11.51 9.56 6.58 01/08/2008 3:05:29 PM RUN6 - 1 11.47 9.56 6.98 01/08/2008 3:05:59 PM RUN6 - 1 11.43 9.56 7.21 01/08/2008 3:06:29 PM RUN6 - 1 11.47 9.56 6.84 01/08/2008 3:06:59 PM RUN6 - 1 11.5 9.55 6.67 01/08/2008 3:07:29 PM RUN6 - 1 11.51 9.54 6.79 01/08/2008 3:07:59 PM RUN6 - 1 11.5 9.56 6.68 01/08/2008 3:08:29 PM RUN6 - 1 11.51 9.57 6.55 01/08/2008 3:08:59 PM RUN6 - 1 11.53 9.54 6.52 01/08/2008 3:09:29 PM RUN6 - 1 11.53 9.52 6.58 01/08/2008 3:09:59 PM RUN6 - 1 11.53 9.53 6.46 01/08/2008 3:10:29 PM RUN6 - 1 11.54 9.51 6.45 01/08/2008 3:10:59 PM RUN6 - 1 11.52 9.53 6.47 01/08/2008 3:11:29 PM RUN6 - 1 11.52 9.55 6.38 01/08/2008 3:11:59 PM RUN6 - 1 11.55 9.54 6.32 01/08/2008 3:12:29 PM RUN6 - 1 11.54 9.54 6.22 01/08/2008 3:12:59 PM RUN6 - 1 11.55 9.52 6.25 01/08/2008 3:13:29 PM RUN6 - 1 11.55 9.52 6.18



### Page 24 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 3:13:59 PM RUN6 - 1 11.56 9.52 6.26 01/08/2008 3:14:29 PM RUN6 - 1 11.54 9.51 6.44 01/08/2008 3:14:59 PM RUN6 - 1 11.53 9.51 6.47 01/08/2008 3:15:29 PM RUN6 - 1 11.52 9.51 6.73 01/08/2008 3:15:59 PM RUN6 - 1 11.46 9.53 6.77 01/08/2008 3:16:29 PM RUN6 - 1 11.51 9.53 6.52 01/08/2008 3:16:59 PM 11.54 9.53 6.45 01/08/2008 3:17:29 PM 10.38 9.36 1.82 01/08/2008 3:17:59 PM 0.2 3.93 -0.09 01/08/2008 3:18:29 PM 0.05 3.72 -0.13 01/08/2008 3:18:59 PM 0.03 3.71 -0.11 01/08/2008 3:19:29 PM 0.03 3.7 -0.13 01/08/2008 3:19:59 PM - Span 0.03 3.69 -0.11 01/08/2008 3:20:29 PM - ZERO 0.03 3.69 -0.12 01/08/2008 3:20:59 PM - ZERO 0.03 3.69 -0.1 01/08/2008 3:21:29 PM - ZERO 0.04 3.68 3.61 01/08/2008 3:21:59 PM - ZERO 0.03 0.18 7.89 01/08/2008 3:22:29 PM - Span 0.04 0.02 7.96 01/08/2008 3:22:59 PM - Span 0.03 0.01 7.96 01/08/2008 3:23:29 PM - Span 2.93 1.45 3.33 01/08/2008 3:23:59 PM - Span 10.03 8.31 0.15 01/08/2008 3:24:29 PM - Span 10.5 9.2 0 01/08/2008 3:24:59 PM - ZERO 10.5 9.21 -0.01 01/08/2008 3:25:29 PM - ZERO 10.5 9.23 -0.02 01/08/2008 3:25:59 PM - ZERO 10.49 9.26 1.78 01/08/2008 3:26:29 PM - ZERO 11.26 9.49 1.82 01/08/2008 3:26:59 PM - ZERO 10.51 9.28 1.92 01/08/2008 3:27:29 PM - ZERO 10.97 9.47 5.49 01/08/2008 3:27:59 PM - ZERO 0.4 0.83 7.85 01/08/2008 3:28:29 PM - ZERO 0.06 0.06 7.96 01/08/2008 3:28:59 PM - ZERO 0.05 0.02 8.06 01/08/2008 3:29:29 PM - ZERO 0.04 0 7.97 01/08/2008 3:29:59 PM - ZERO 0.02 0 7.67 01/08/2008 3:30:29 PM - ZERO 6.98 5.25 2.12 01/08/2008 3:30:59 PM - ZERO 11.06 9.15 6.23 01/08/2008 3:31:29 PM - ZERO 11.44 9.49 5.91 01/08/2008 3:31:59 PM - ZERO 11.53 9.53 6.53 01/08/2008 3:32:29 PM - ZERO 11.54 9.54 6.46 01/08/2008 3:32:59 PM RUN7 - 1 11.53 9.53 6.52 01/08/2008 3:33:29 PM RUN7 - 1 11.54 9.53 6.53



### Page 25 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 3:33:59 PM RUN7 - 1 11.52 9.54 6.67 01/08/2008 3:34:29 PM RUN7 - 1 11.52 9.54 6.64 01/08/2008 3:34:59 PM RUN7 - 1 11.52 9.55 6.77 01/08/2008 3:35:29 PM RUN7 - 1 11.51 9.55 6.87 01/08/2008 3:35:59 PM RUN7 - 1 11.49 9.57 6.69 01/08/2008 3:36:29 PM RUN7 - 1 11.5 9.55 6.72 01/08/2008 3:36:59 PM RUN7 - 1 11.52 9.55 6.68 01/08/2008 3:37:29 PM RUN7 - 1 11.52 9.55 6.66 01/08/2008 3:37:59 PM RUN7 - 1 11.52 9.55 6.54 01/08/2008 3:38:29 PM RUN7 - 1 11.52 9.56 6.53 01/08/2008 3:38:59 PM RUN7 - 1 11.51 9.54 6.55 01/08/2008 3:39:29 PM RUN7 - 1 11.51 9.51 6.74 01/08/2008 3:39:59 PM RUN7 - 1 11.54 9.52 6.69 01/08/2008 3:40:29 PM RUN7 - 1 11.5 9.54 6.83 01/08/2008 3:40:59 PM RUN7 - 1 11.49 9.51 7.1 01/08/2008 3:41:29 PM RUN7 - 1 11.48 9.54 7.04 01/08/2008 3:41:59 PM RUN7 - 1 11.47 9.53 7.1 01/08/2008 3:42:29 PM RUN7 - 1 11.49 9.54 6.96 01/08/2008 3:42:59 PM RUN7 - 1 11.49 9.52 7.09 01/08/2008 3:43:29 PM RUN7 - 1 11.49 9.53 7.01 01/08/2008 3:43:59 PM RUN7 - 1 11.48 9.52 6.95 01/08/2008 3:44:29 PM RUN7 - 1 11.5 9.52 6.77 01/08/2008 3:44:59 PM RUN7 - 1 11.5 9.53 6.74 01/08/2008 3:45:29 PM RUN7 - 1 11.49 9.55 7 01/08/2008 3:45:59 PM RUN7 - 1 11.43 9.57 7.24 01/08/2008 3:46:29 PM RUN7 - 1 11.46 9.59 6.81 01/08/2008 3:46:59 PM RUN7 - 1 11.52 9.57 6.45 01/08/2008 3:47:29 PM RUN7 - 1 11.52 9.57 6.52 01/08/2008 3:47:59 PM RUN7 - 1 11.54 9.57 6.48 01/08/2008 3:48:29 PM RUN7 - 1 11.53 9.55 6.54 01/08/2008 3:48:59 PM RUN7 - 1 11.52 9.58 6.7 01/08/2008 3:49:29 PM RUN7 - 1 11.52 9.55 6.67 01/08/2008 3:49:59 PM RUN7 - 1 11.52 9.59 6.41 01/08/2008 3:50:29 PM RUN7 - 1 11.53 9.56 6.54 01/08/2008 3:50:59 PM RUN7 - 1 11.51 9.53 6.74 01/08/2008 3:51:29 PM RUN7 - 1 11.51 9.54 6.69 01/08/2008 3:51:59 PM RUN7 - 1 11.53 9.55 6.58 01/08/2008 3:52:29 PM RUN7 - 1 11.55 9.54 6.51 01/08/2008 3:52:59 PM RUN7 - 1 11.55 9.54 6.41 01/08/2008 3:53:29 PM RUN7 - 1 11.55 9.52 6.51



### Page 26 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 3:53:59 PM 11.52 9.54 6.48 01/08/2008 3:54:29 PM 11.55 9.53 5.96 01/08/2008 3:54:59 PM 1.06 4.28 0.41 01/08/2008 3:55:29 PM 0.05 3.69 -0.11 01/08/2008 3:55:59 PM 0.04 3.69 -0.12 01/08/2008 3:56:29 PM 0.04 3.68 -0.12 01/08/2008 3:56:59 PM 0.03 3.67 -0.12 01/08/2008 3:57:29 PM - ZERO 0.02 3.67 -0.13 01/08/2008 3:57:59 PM - ZERO 0.03 3.66 -0.11 01/08/2008 3:58:29 PM - ZERO 0.03 3.58 4.17 01/08/2008 3:58:59 PM - Span 0.04 0.08 7.91 01/08/2008 3:59:29 PM - Span 0.02 0.01 7.94 01/08/2008 3:59:59 PM - Span 0.03 0 7.95 01/08/2008 4:00:29 PM - ZERO 0.04 -0.01 7.95 01/08/2008 4:00:59 PM - ZERO 0.02 -0.01 7.55 01/08/2008 4:01:29 PM - ZERO 7.43 5.5 1.21 01/08/2008 4:01:59 PM - ZERO 10.44 9.05 -0.01 01/08/2008 4:02:29 PM - ZERO 10.5 9.19 -0.02 01/08/2008 4:02:59 PM - ZERO 10.49 9.22 -0.02 01/08/2008 4:03:59 PM 11.53 9.47 6.07 01/08/2008 4:04:29 PM 11.58 9.49 6.15 01/08/2008 4:04:59 PM 11.58 9.49 6.16 01/08/2008 4:05:29 PM 11.57 9.47 6.32 01/08/2008 4:05:59 PM 11.59 9.5 6.22 01/08/2008 4:06:29 PM 11.55 9.47 6.51 01/08/2008 4:06:59 PM 11.56 9.49 6.42 01/08/2008 4:07:29 PM 11.55 9.49 6.44 01/08/2008 4:07:59 PM RUN8 - 1 11.54 9.51 6.46 01/08/2008 4:08:29 PM RUN8 - 1 11.56 9.5 6.34 01/08/2008 4:08:59 PM RUN8 - 1 11.55 9.5 6.4 01/08/2008 4:09:29 PM RUN8 - 1 11.56 9.49 6.4 01/08/2008 4:09:59 PM RUN8 - 1 11.57 9.5 6.3 01/08/2008 4:10:29 PM RUN8 - 1 11.52 9.5 6.63 01/08/2008 4:10:59 PM RUN8 - 1 11.46 9.5 6.84 01/08/2008 4:11:29 PM RUN8 - 1 11.47 9.51 6.89 01/08/2008 4:11:59 PM RUN8 - 1 11.52 9.5 6.61 01/08/2008 4:12:29 PM RUN8 - 1 11.54 9.48 6.67 01/08/2008 4:12:59 PM RUN8 - 1 11.53 9.49 6.6 01/08/2008 4:13:29 PM RUN8 - 1 11.53 9.5 6.66 01/08/2008 4:13:59 PM RUN8 - 1 11.52 9.5 6.68



### Page 27 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 4:14:29 PM RUN8 - 1 11.5 9.48 6.85 01/08/2008 4:14:59 PM RUN8 - 1 11.5 9.51 6.93 01/08/2008 4:15:29 PM RUN8 - 1 11.49 9.53 6.87 01/08/2008 4:15:59 PM RUN8 - 1 11.48 9.52 6.92 01/08/2008 4:16:29 PM RUN8 - 1 11.47 9.51 7.12 01/08/2008 4:16:59 PM RUN8 - 1 11.46 9.52 7.05 01/08/2008 4:17:29 PM RUN8 - 1 11.47 9.5 7.08 01/08/2008 4:17:59 PM RUN8 - 1 11.46 9.52 7.07 01/08/2008 4:18:29 PM RUN8 - 1 11.49 9.52 6.95 01/08/2008 4:18:59 PM RUN8 - 1 11.51 9.51 6.85 01/08/2008 4:19:29 PM RUN8 - 1 11.48 9.52 6.95 01/08/2008 4:19:59 PM RUN8 - 1 11.48 9.5 7.03 01/08/2008 4:20:29 PM RUN8 - 1 11.48 9.52 7.07 01/08/2008 4:20:59 PM RUN8 - 1 11.48 9.52 7.14 01/08/2008 4:21:29 PM RUN8 - 1 11.46 9.52 7.29 01/08/2008 4:21:59 PM RUN8 - 1 11.46 9.5 7.42 01/08/2008 4:22:29 PM RUN8 - 1 11.43 9.52 7.46 01/08/2008 4:22:59 PM RUN8 - 1 11.44 9.51 7.42 01/08/2008 4:23:29 PM RUN8 - 1 11.46 9.51 7.21 01/08/2008 4:23:59 PM RUN8 - 1 11.46 9.51 7.12 01/08/2008 4:24:29 PM RUN8 - 1 11.47 9.51 7.3 01/08/2008 4:24:59 PM RUN8 - 1 11.47 9.54 7.02 01/08/2008 4:25:29 PM RUN8 - 1 11.48 9.52 7.13 01/08/2008 4:25:59 PM RUN8 - 1 11.42 9.53 7.37 01/08/2008 4:26:29 PM RUN8 - 1 11.44 9.52 7.13 01/08/2008 4:26:59 PM RUN8 - 1 11.49 9.5 6.93 01/08/2008 4:27:29 PM RUN8 - 1 11.5 9.49 7.03 01/08/2008 4:27:59 PM RUN8 - 1 11.48 9.5 7.08 01/08/2008 4:28:29 PM RUN8 - 1 11.51 9.5 6.89 01/08/2008 4:28:59 PM 11.5 9.51 6.85 01/08/2008 4:29:29 PM 11.5 9.49 5.9 01/08/2008 4:29:59 PM 2.45 5.6 0.33 01/08/2008 4:30:29 PM 0.04 3.72 -0.12 01/08/2008 4:30:59 PM - Span 0.03 3.69 -0.1 01/08/2008 4:31:29 PM - ZERO 0.03 3.68 -0.1 01/08/2008 4:31:59 PM - ZERO 0.03 3.68 -0.12 01/08/2008 4:32:29 PM - ZERO 0.03 2.55 5.94 01/08/2008 4:32:59 PM - ZERO 0.03 0.04 7.96 01/08/2008 4:33:29 PM - Span 0.04 0.02 7.98 01/08/2008 4:33:59 PM - Span 0.03 0.01 7.96



### Page 28 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 4:34:29 PM - Span 6.25 4.49 1.88 01/08/2008 4:34:59 PM - Span 10.39 8.92 0.05 01/08/2008 4:35:29 PM - ZERO 10.48 9.2 0.02 01/08/2008 4:35:59 PM - ZERO 10.48 9.22 0.01 01/08/2008 4:36:29 PM - ZERO 10.48 9.23 0.02 01/08/2008 4:36:59 PM - ZERO 11.07 9.33 4.13 01/08/2008 4:37:29 PM - ZERO 11.49 9.45 6.57 01/08/2008 4:37:59 PM - ZERO 11.5 9.49 6.7 01/08/2008 4:38:29 PM - ZERO 11.52 9.48 6.7 01/08/2008 4:38:59 PM - ZERO 11.49 9.48 6.79 01/08/2008 4:39:29 PM run9 - 1 11.5 9.5 6.78 01/08/2008 4:39:59 PM run9 - 1 11.51 9.48 6.74 01/08/2008 4:40:29 PM run9 - 1 11.49 9.48 6.86 01/08/2008 4:40:59 PM run9 - 1 11.49 9.5 6.92 01/08/2008 4:41:29 PM run9 - 1 11.48 9.47 7.01 01/08/2008 4:41:59 PM run9 - 1 11.49 9.49 6.91 01/08/2008 4:42:29 PM run9 - 1 11.52 9.49 6.69 01/08/2008 4:42:59 PM run9 - 1 11.51 9.48 6.91 01/08/2008 4:43:29 PM run9 - 1 11.5 9.52 6.79 01/08/2008 4:43:59 PM run9 - 1 11.51 9.5 6.81 01/08/2008 4:44:29 PM run9 - 1 11.49 9.49 6.96 01/08/2008 4:44:59 PM run9 - 1 11.52 9.49 6.92 01/08/2008 4:45:29 PM run9 - 1 11.53 9.5 6.82 01/08/2008 4:45:59 PM run9 - 1 11.52 9.49 6.89 01/08/2008 4:46:29 PM run9 - 1 11.51 9.49 6.87 01/08/2008 4:46:59 PM run9 - 1 11.52 9.49 6.89 01/08/2008 4:47:29 PM run9 - 1 11.53 9.49 6.61 01/08/2008 4:47:59 PM run9 - 1 11.53 9.49 6.72 01/08/2008 4:48:29 PM run9 - 1 11.52 9.49 6.83 01/08/2008 4:48:59 PM run9 - 1 11.52 9.49 6.72 01/08/2008 4:49:29 PM run9 - 1 11.53 9.49 6.81 01/08/2008 4:49:59 PM run9 - 1 11.51 9.49 6.95 01/08/2008 4:50:29 PM run9 - 1 11.51 9.47 6.99 01/08/2008 4:50:59 PM run9 - 1 11.45 9.49 7.44 01/08/2008 4:51:29 PM run9 - 1 11.43 9.51 7.37 01/08/2008 4:51:59 PM run9 - 1 11.51 9.48 6.88 01/08/2008 4:52:29 PM run9 - 1 11.51 9.5 6.81 01/08/2008 4:52:59 PM run9 - 1 11.51 9.47 6.72 01/08/2008 4:53:29 PM run9 - 1 11.53 9.49 6.71 01/08/2008 4:53:59 PM run9 - 1 11.54 9.49 6.68



### Page 29 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 4:54:29 PM run9 - 1 11.54 9.47 6.63 01/08/2008 4:54:59 PM run9 - 1 11.55 9.48 6.72 01/08/2008 4:55:29 PM run9 - 1 11.53 9.51 6.58 01/08/2008 4:55:59 PM run9 - 1 11.53 9.47 6.69 01/08/2008 4:56:29 PM run9 - 1 11.52 9.47 6.76 01/08/2008 4:56:59 PM run9 - 1 11.51 9.49 6.86 01/08/2008 4:57:29 PM run9 - 1 11.51 9.48 6.8 01/08/2008 4:57:59 PM run9 - 1 11.54 9.46 6.59 01/08/2008 4:58:29 PM run9 - 1 11.54 9.48 6.69 01/08/2008 4:58:59 PM run9 - 1 11.53 9.48 6.64 01/08/2008 4:59:29 PM run9 - 1 11.55 9.46 6.56 01/08/2008 4:59:59 PM run9 - 1 11.55 9.47 6.74 01/08/2008 5:00:29 PM 11.53 9.49 6.77 01/08/2008 5:00:59 PM 11.53 9.51 6.01 01/08/2008 5:01:29 PM 2.83 5.85 0.4 01/08/2008 5:01:59 PM 0.06 3.73 -0.11 01/08/2008 5:02:29 PM 0.04 3.71 -0.13 01/08/2008 5:02:59 PM - ZERO 0.05 3.69 -0.1 01/08/2008 5:03:29 PM - ZERO 0.03 3.69 -0.11 01/08/2008 5:03:59 PM - ZERO 0.04 3.27 4.61 01/08/2008 5:04:29 PM - Span 0.03 0.07 7.94 01/08/2008 5:04:59 PM - ZERO 0.03 0.02 7.98 01/08/2008 5:05:29 PM - ZERO 0.04 0 7.8 01/08/2008 5:05:59 PM - ZERO 7.66 5.72 1.46 01/08/2008 5:06:29 PM - ZERO 10.46 9.08 0.04 01/08/2008 5:06:59 PM - Span 10.5 9.22 -0.01 01/08/2008 5:07:29 PM - ZERO 10.49 9.22 0.03 01/08/2008 5:07:59 PM - ZERO 10.49 9.24 -0.01 01/08/2008 5:08:29 PM - ZERO 17.48 4.74 0.12 01/08/2008 5:08:59 PM - ZERO 14.89 4.12 0.03 01/08/2008 5:09:29 PM - ZERO 20.27 1.31 0.18 01/08/2008 5:09:59 PM - ZERO 20.87 0.1 0.25 01/08/2008 5:10:29 PM - ZERO 20.87 0.07 0.22 01/08/2008 5:10:59 PM - ZERO 20.87 0.06 0.24 01/08/2008 5:11:29 PM - ZERO 20.88 0.06 0.25 01/08/2008 5:11:59 PM - ZERO 20.88 0.05 0.23 01/08/2008 5:12:29 PM - ZERO 20.89 0.03 0.23 01/08/2008 5:12:59 PM - ZERO 20.88 0.05 0.24 01/08/2008 5:13:29 PM - ZERO 20.9 0.02 0.24 01/08/2008 5:13:59 PM - ZERO 20.91 0.03 0.24



### Page 30 of 31

### LabView Run Log

Date Time Status aO2 (%) bCO2 (PPM ) cCO (PPM)

01/08/2008 5:14:29 PM - ZERO 20.91 0.02 0.27 01/08/2008 5:14:59 PM - ZERO 20.9 0.02 0.23 01/08/2008 5:15:29 PM - ZERO 20.88 0.02 0.27 01/08/2008 5:15:59 PM - ZERO 20.84 0.01 0.27 01/08/2008 5:16:29 PM - ZERO 20.8 0.01 0.29 01/08/2008 5:16:59 PM - ZERO 20.78 0 0.31 01/08/2008 5:17:29 PM - ZERO 20.76 0 0.28 01/08/2008 5:17:59 PM - ZERO 20.73 0.01 0.32 01/08/2008 5:18:29 PM - ZERO 20.75 0 0.33 01/08/2008 5:18:59 PM - ZERO 20.7 0.03 0.36 01/08/2008 5:19:29 PM - ZERO 20.71 0.04 0.33



### Page 31 of 31

### CYLINDER GAS CERTIFICATES

## APPENDIX B

TURBINE DATA

### Plant Information Database Query Results

Plant Information Source: polk-1pisr v Start Time: 01/08/2008 10:4 6

End Time: 01/08/2008 17:0 0 Time Interval: 1 Min

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 10:46:0 0 179.1152649 7131.78759 8 72.70927 4 1.29266 08-Jan-08 10:47:0 0 178.963256 8 7064.672852 72.632591 1.29276 08-Jan-08 10:48:0 0 178.2445831 7062.369141 72.555908 1.29287 08-Jan-08 10:49:0 0 178.1081543 7099.312012 72.574768 1.29297 08-Jan-08 10:50:0 0 178.7349701 7150.769531 72.880249 1.29307 08-Jan-08 10:51:0 0 179.2855682 7111.02050 8 73.062531 1.29317 08-Jan-08 10:52:0 0 179.4393463 7082.110352 72.751999 1.29327 08-Jan-08 10:53:0 0 177.88797 7049.321289 72.862427 1.29338 08-Jan-08 10:54:0 0 178.4517975 7064.905273 73.167915 1.29348 08-Jan-08 10:55:0 0 180.3786163 7102.365723 73.3647 1.29358 08-Jan-08 10:56:0 0 179.5168152 7098.838379 73.136871 1.29368 08-Jan-08 10:57:0 0 180.119751 7085.383301 73.25927 1.29378 08-Jan-08 10:58:0 0 180.419632 7064.53857 4 73.38166 1.29389 08-Jan-08 10:59:0 0 178.834945 7 7062.338379 73.504051 1.29399 08-Jan-08 11:00:0 0 178.884887 7 7086.172852 73.626442 1.29409 08-Jan-08 11:01:0 0 178.3968201 7076.08886 7 73.7488 4 1.29419 08-Jan-08 11:02:0 0 178.3382721 7052.737305 74.35659 1.29429 08-Jan-08 11:03:0 0 178.164611 8 7036.25293 74.451248 1.2944 08-Jan-08 11:04:0 0 178.0582123 7076.700195 74.527931 1.2945 08-Jan-08 11:05:0 0 179.8825073 7172.99023 4 74.60461 4 1.2946 08-Jan-08 11:06:0 0 178.8912659 7074.12109 4 74.68129 1.2947 08-Jan-08 11:07:0 0 178.7831573 7061.745605 74.418182 1.2948 08-Jan-08 11:08:0 0 178.5129852 7080.81298 8 74.644043 1.29491 08-Jan-08 11:09:0 0 178.270721 4 7085.19482 4 74.426285 1.29501 08-Jan-08 11:10:0 0 179.6755829 7120.695313 74.115753 1.29511 08-Jan-08 11:11:0 0 179.576522 8 7117.541992 74.501862 1.29521 08-Jan-08 11:12:0 0 178.4888153 7104.06054 7 74.654602 1.29531 08-Jan-08 11:13:0 0 178.8935242 7124.995605 74.611099 1.29541 08-Jan-08 11:14:0 0 178.45524 6 8221.917969 74.50787 4 1.29552 08-Jan-08 11:15:0 0 178.3178253 7182.096191 74.404648 1.29562 08-Jan-08 11:16:0 0 179.283996 6 7127.008301 74.288399 1.29572 08-Jan-08 11:17:0 0 179.3051605 7100.53418 74.761711 1.29582 08-Jan-08 11:18:0 0 178.368560 8 7085.14502 74.863815 1.29592 08-Jan-08 11:19:0 0 177.9571991 7062.21972 7 74.965919 1.29603 08-Jan-08 11:20:0 0 179.1837463 7103.149902 74.8853 1.29613 08-Jan-08 11:21:0 0 179.148162 8 7110.525391 75.193283 1.29623 08-Jan-08 11:22:0 0 179.6767883 7112.26806 6 75.091339 1.29633 08-Jan-08 11:23:0 0 178.7565002 7090.67089 8 75.246605 1.29643 08-Jan-08 11:24:0 0 179.379562 4 7115.965332 75.541046 1.29654 08-Jan-08 11:25:0 0 179.4131012 7107.12841 8 75.391335 1.29664



### Page 1 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 11:26:0 0 178.423385 6 7056.306641 75.463776 1.29674 08-Jan-08 11:27:0 0 179.159820 6 7109.922852 75.481163 1.29684 08-Jan-08 11:28:0 0 178.674881 7087.876465 75.407585 1.29694 08-Jan-08 11:29:0 0 177.7310181 7132.04443 4 75.610062 1.29705 08-Jan-08 11:30:0 0 179.1592712 7250.27636 7 75.812538 1.29715 08-Jan-08 11:31:0 0 179.312423 7 7148.35058 6 75.691055 1.29725 08-Jan-08 11:32:0 0 179.3832245 7117.10839 8 75.051193 1.29735 08-Jan-08 11:33:0 0 179.556121 8 7133.24218 8 75.18166 4 1.29745 08-Jan-08 11:34:0 0 178.7237091 7111.98681 6 75.312126 1.29755 08-Jan-08 11:35:0 0 178.5356445 7110.65429 7 75.442596 1.29766 08-Jan-08 11:36:0 0 177.55389 4 7096.928223 75.573059 1.29776 08-Jan-08 11:37:0 0 178.2543793 7070.22216 8 75.703529 1.29786 08-Jan-08 11:38:0 0 177.752929 7 7091.64843 8 75.834 1.29796 08-Jan-08 11:39:0 0 178.598053 7087.12597 7 75.863312 1.29806 08-Jan-08 11:40:0 0 179.4431763 7111.77929 7 75.682495 1.29817 08-Jan-08 11:41:0 0 179.382003 8 7092.186035 75.87788 4 1.29827 08-Jan-08 11:42:0 0 178.309127 8 7073.497559 75.571663 1.29837 08-Jan-08 11:43:0 0 179.0954895 7067.630859 74.98006 4 1.29847 08-Jan-08 11:44:0 0 179.298111 7125.78173 8 74.824799 1.29857 08-Jan-08 11:45:0 0 178.4942322 7205.20752 74.417679 1.29868 08-Jan-08 11:46:0 0 179.5084229 7140.42041 74.823257 1.29878 08-Jan-08 11:47:0 0 179.09115 6 7142.470215 75.228836 1.29888 08-Jan-08 11:48:0 0 179.9411011 7153.193359 75.615906 1.29898 08-Jan-08 11:49:0 0 179.366134 6 7132.973145 75.466187 1.29908 08-Jan-08 11:50:0 0 178.407959 7119.45459 75.316475 1.29919 08-Jan-08 11:51:0 0 178.2354431 7120.18798 8 75.517845 1.29929 08-Jan-08 11:52:0 0 177.7017365 7095.840332 75.719223 1.29939 08-Jan-08 11:53:0 0 178.0559692 7095.058105 75.920593 1.29949 08-Jan-08 11:54:0 0 179.4611053 7125.92724 6 75.651199 1.29959 08-Jan-08 11:55:0 0 179.1287689 7195.42431 6 75.898087 1.2997 08-Jan-08 11:56:0 0 179.6149445 7133.376465 76.206078 1.2998 08-Jan-08 11:57:0 0 180.3777161 7125.12011 7 76.069191 1.2999 08-Jan-08 11:58:0 0 180.017501 8 7124.411133 75.863861 1.3 08-Jan-08 11:59:0 0 179.6572723 7115.525391 75.658539 1.3001 08-Jan-08 12:00:0 0 179.5390015 7122.418945 75.620895 1.3002 08-Jan-08 12:01:0 0 178.1641693 7123.94384 8 75.620895 1.30031 08-Jan-08 12:02:0 0 177.8606873 7135.967773 75.316475 1.30041 08-Jan-08 12:03:0 0 179.5675201 7138.8891 6 75.749657 1.30051 08-Jan-08 12:04:0 0 180.497329 7 7153.019531 75.9252 4 1.30061 08-Jan-08 12:05:0 0 180.4523163 7144.951172 76.100815 1.30071 08-Jan-08 12:06:0 0 179.7201843 7123.94043 76.276398 1.30082 08-Jan-08 12:07:0 0 179.115097 7112.94043 76.451981 1.30092 08-Jan-08 12:08:0 0 178.3156433 7099.37304 7 76.627563 1.30102 08-Jan-08 12:09:0 0 178.1337891 7122.26123 76.803139 1.30112 08-Jan-08 12:10:0 0 179.434539 8 7229.396973 77.186501 1.30122



### Page 2 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 12:11:0 0 179.713424 7 7107.587402 77.186501 1.30133 08-Jan-08 12:12:0 0 179.1413879 7094.539063 76.790565 1.30143 08-Jan-08 12:13:0 0 179.1005249 7023.94433 6 76.6353 1.30153 08-Jan-08 12:14:0 0 179.204742 4 7102.599609 76.821762 1.30163 08-Jan-08 12:15:0 0 178.6329193 7112.316895 76.718536 1.30173 08-Jan-08 12:16:0 0 179.3988495 7112.90332 76.615311 1.30184 08-Jan-08 12:17:0 0 180.294860 8 7084.37597 7 76.647522 1.30194 08-Jan-08 12:18:0 0 179.6038513 7093.83593 8 77.143959 1.30204 08-Jan-08 12:19:0 0 178.672683 7 7126.287109 77.041847 1.30214 08-Jan-08 12:20:0 0 178.673431 4 7116.937012 76.939743 1.30224 08-Jan-08 12:21:0 0 178.4564209 7113.343262 76.763786 1.30235 08-Jan-08 12:22:0 0 177.754699 7 7107.98974 6 76.873375 1.30245 08-Jan-08 12:23:0 0 178.4224701 7099.754395 76.873375 1.30255 08-Jan-08 12:24:0 0 179.0210419 7160.56591 8 77.125237 1.30265 08-Jan-08 12:25:0 0 178.995025 6 7225.50732 4 76.921028 1.30275 08-Jan-08 12:26:0 0 178.821380 6 7092.5766 6 76.71682 1.30285 08-Jan-08 12:27:0 0 177.9845581 7112.191895 76.701668 1.30296 08-Jan-08 12:28:0 0 178.4194489 7135.109375 76.998627 1.30306 08-Jan-08 12:29:0 0 178.2599182 7129.36132 8 76.588486 1.30316 08-Jan-08 12:30:0 0 178.567016 6 7162.43017 6 76.742485 1.30326 08-Jan-08 12:31:0 0 178.8016052 7122.247559 76.850082 1.30336 08-Jan-08 12:32:0 0 179.3899689 7187.681641 76.694817 1.30347 08-Jan-08 12:33:0 0 179.4660645 7145.904785 76.873375 1.30357 08-Jan-08 12:34:0 0 179.561142 7163 76.570412 1.30367 08-Jan-08 12:35:0 0 179.5748749 7191.40966 8 76.671967 1.30377 08-Jan-08 12:36:0 0 179.1436615 7105.33886 7 76.77351 4 1.30387 08-Jan-08 12:37:0 0 177.9611359 7069.89209 76.865677 1.30398 08-Jan-08 12:38:0 0 177.965896 6 7106.193359 76.403702 1.30408 08-Jan-08 12:39:0 0 178.909515 4 7082.579102 75.941719 1.30418 08-Jan-08 12:40:0 0 178.1005249 7116.460449 76.335632 1.30428 08-Jan-08 12:41:0 0 179.410827 6 7097.209473 76.744049 1.30438 08-Jan-08 12:42:0 0 179.5126495 7104.848633 77.152466 1.30449 08-Jan-08 12:43:0 0 179.450119 7119.27148 4 76.339539 1.30459 08-Jan-08 12:44:0 0 179.432113 6 7133.69433 6 76.384605 1.30469 08-Jan-08 12:45:0 0 179.8762512 7123.079102 76.537346 1.30479 08-Jan-08 12:46:0 0 178.3610992 7108.044922 77.092567 1.30489 08-Jan-08 12:47:0 0 178.186767 6 7093.63476 6 77.002769 1.305 08-Jan-08 12:48:0 0 178.7910309 7079.33398 4 77.158035 1.3051 08-Jan-08 12:49:0 0 178.453323 4 7096.512695 76.998627 1.3052 08-Jan-08 12:50:0 0 178.115615 8 7176.925781 77.066849 1.3053 08-Jan-08 12:51:0 0 178.839141 8 7087.21191 4 76.914108 1.3054 08-Jan-08 12:52:0 0 179.271392 8 7079.08349 6 76.761368 1.3055 08-Jan-08 12:53:0 0 179.4935303 7087.33398 4 76.608627 1.30561 08-Jan-08 12:54:0 0 179.7006531 7118.92968 8 76.77071 4 1.30571 08-Jan-08 12:55:0 0 179.653030 4 7127.42431 6 76.668053 1.30581



### Page 3 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 12:56:0 0 179.577102 7 7134.14648 4 76.483261 1.30591 08-Jan-08 12:57:0 0 179.611648 6 7084.30859 4 76.342888 1.30601 08-Jan-08 12:58:0 0 178.136581 4 7078.625 76.49815 4 1.30612 08-Jan-08 12:59:0 0 178.435989 4 7079.32763 7 76.247139 1.30622 08-Jan-08 13:00:0 0 178.4160309 7110.251465 76.247139 1.30632 08-Jan-08 13:01:0 0 179.38591 7132.618652 76.247139 1.30642 08-Jan-08 13:02:0 0 179.9172363 7132.92431 6 76.247139 1.30652 08-Jan-08 13:03:0 0 179.6038513 7081.078125 76.336967 1.30663 08-Jan-08 13:04:0 0 178.65748 6 7123.135742 75.874985 1.30673 08-Jan-08 13:05:0 0 178.5965881 7145.757813 75.759491 1.30683 08-Jan-08 13:06:0 0 178.3741302 7114.957031 76.067482 1.30693 08-Jan-08 13:07:0 0 178.7499695 7088.574219 75.990479 1.30703 08-Jan-08 13:08:0 0 179.2937469 7092.14941 4 75.98452 1.30714 08-Jan-08 13:09:0 0 178.9767609 7123.390625 76.560257 1.30724 08-Jan-08 13:10:0 0 179.347808 8 7142.641602 76.560257 1.30734 08-Jan-08 13:11:0 0 179.2598419 7116.99804 7 76.560257 1.30744 08-Jan-08 13:12:0 0 178.986663 8 7096.30517 6 76.375465 1.30754 08-Jan-08 13:13:0 0 178.713501 7095.69726 6 75.934021 1.30764 08-Jan-08 13:14:0 0 178.922088 6 7126.09472 7 76.057213 1.30775 08-Jan-08 13:15:0 0 179.680465 7 7219.578613 76.519196 1.30785 08-Jan-08 13:16:0 0 179.647216 8 7147.078125 76.80151 4 1.30795 08-Jan-08 13:17:0 0 179.0704193 7099.77636 7 76.658737 1.30805 08-Jan-08 13:18:0 0 178.3297272 7062.057129 77.113266 1.30815 08-Jan-08 13:19:0 0 178.8196259 7068.29052 7 77.476517 1.30826 08-Jan-08 13:20:0 0 179.289825 4 7115.78808 6 77.322525 1.30836 08-Jan-08 13:21:0 0 180.3114471 7139.94043 77.222435 1.30846 08-Jan-08 13:22:0 0 180.2920685 7136.175293 77.468819 1.30856 08-Jan-08 13:23:0 0 178.925293 7094.300781 77.160828 1.30866 08-Jan-08 13:24:0 0 177.4853973 7081.467285 76.580788 1.30877 08-Jan-08 13:25:0 0 177.7691193 7077.922363 76.9914 4 1.30887 08-Jan-08 13:26:0 0 178.0528412 7097.23388 7 77.40208 4 1.30897 08-Jan-08 13:27:0 0 178.226455 7 7109.15136 7 77.812737 1.30907 08-Jan-08 13:28:0 0 179.49563 6 7117.792969 77.710632 1.30917 08-Jan-08 13:29:0 0 179.2988892 7144.422852 77.608528 1.30928 08-Jan-08 13:30:0 0 179.022384 6 7208.485352 77.50642 4 1.30938 08-Jan-08 13:31:0 0 178.7661285 7127.482422 77.216805 1.30948 08-Jan-08 13:32:0 0 178.9600983 7109.73388 7 77.352272 1.30958 08-Jan-08 13:33:0 0 178.722503 7 7092.687012 77.536461 1.30968 08-Jan-08 13:34:0 0 178.0629883 7088.268555 77.72065 1.30979 08-Jan-08 13:35:0 0 178.8065643 7133.227539 77.904839 1.30989 08-Jan-08 13:36:0 0 179.004684 4 7132.681641 78.089027 1.30999 08-Jan-08 13:37:0 0 179.1823883 7130.02734 4 77.63308 1.31009 08-Jan-08 13:38:0 0 178.155761 7 6892.980469 77.499619 1.31019 08-Jan-08 13:39:0 0 179.564529 4 7126.834473 77.812737 1.31029 08-Jan-08 13:40:0 0 179.3068085 7134.351563 78.221153 1.3104



### Page 4 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 13:41:0 0 178.9916229 7140.251465 78.62957 1.3105 08-Jan-08 13:42:0 0 178.3234253 7118.624023 78.752098 1.3106 08-Jan-08 13:43:0 0 178.736709 6 7062.50341 8 78.752098 1.3107 08-Jan-08 13:44:0 0 179.695556 6 7134.51123 78.654572 1.3108 08-Jan-08 13:45:0 0 179.1885071 7227.5766 6 78.43898 1.31091 08-Jan-08 13:46:0 0 179.115509 7187.464355 78.43898 1.31101 08-Jan-08 13:47:0 0 178.4027405 7132.050293 78.125862 1.31111 08-Jan-08 13:48:0 0 177.7938232 7121.704102 78.48518 4 1.31121 08-Jan-08 13:49:0 0 178.6226959 7113.786133 79.101151 1.31131 08-Jan-08 13:50:0 0 179.572616 6 7135.602051 79.378342 1.31142 08-Jan-08 13:51:0 0 178.6563263 7142.286621 79.05249 1.31152 08-Jan-08 13:52:0 0 178.6054382 7126.274902 78.441528 1.31162 08-Jan-08 13:53:0 0 179.1507721 7110.26318 4 78.43898 1.31172 08-Jan-08 13:54:0 0 178.9419403 7133.62011 7 78.6828 1.31182 08-Jan-08 13:55:0 0 180.038818 4 7248.005859 78.528809 1.31193 08-Jan-08 13:56:0 0 179.8782349 7156.575195 78.567307 1.31203 08-Jan-08 13:57:0 0 179.0166931 7091.686523 79.045593 1.31213 08-Jan-08 13:58:0 0 177.9540405 7088.049805 78.9944 1.31223 08-Jan-08 13:59:0 0 178.109695 4 7090.120605 78.94321 4 1.31233 08-Jan-08 14:00:0 0 178.635009 8 7109.823242 78.892021 1.31244 08-Jan-08 14:01:0 0 178.8851471 7122.22216 8 78.840828 1.31254 08-Jan-08 14:02:0 0 179.162429 8 7130.22900 4 78.789635 1.31264 08-Jan-08 14:03:0 0 179.840545 7 7143.438965 78.587837 1.31274 08-Jan-08 14:04:0 0 179.547866 8 7129.32177 7 77.66901 4 1.31284 08-Jan-08 14:05:0 0 179.227630 6 7129.672363 77.319962 1.31294 08-Jan-08 14:06:0 0 179.412246 7 7133.217773 77.935936 1.31305 08-Jan-08 14:07:0 0 178.763031 7111.77929 7 78.551903 1.31315 08-Jan-08 14:08:0 0 177.789093 7089.436035 78.775391 1.31325 08-Jan-08 14:09:0 0 178.14233 4 7122.65722 7 78.930656 1.31335 08-Jan-08 14:10:0 0 178.3154755 7240.23291 78.769989 1.31345 08-Jan-08 14:11:0 0 178.5799713 7146.852051 78.923355 1.31356 08-Jan-08 14:12:0 0 179.0852051 7137.7641 6 79.076721 1.31366 08-Jan-08 14:13:0 0 179.730056 8 7155.744141 79.230087 1.31376 08-Jan-08 14:14:0 0 179.6673431 7157.25683 6 79.373253 1.31386 08-Jan-08 14:15:0 0 180.0613251 7165.873535 79.220505 1.31396 08-Jan-08 14:16:0 0 178.7208099 7097.883789 79.06776 4 1.31407 08-Jan-08 14:17:0 0 178.4838715 7121.39209 79.21664 4 1.31417 08-Jan-08 14:18:0 0 179.350570 7 7121.97900 4 79.37064 4 1.31427 08-Jan-08 14:19:0 0 179.274398 8 7159.54541 78.939461 1.31437 08-Jan-08 14:20:0 0 179.2293701 7175.1108 4 78.477478 1.31447 08-Jan-08 14:21:0 0 179.257766 7 7095.210449 78.721298 1.31458 08-Jan-08 14:22:0 0 179.6072845 7153.911621 78.301826 1.31468 08-Jan-08 14:23:0 0 178.328521 7 7066.04150 4 78.146561 1.31478 08-Jan-08 14:24:0 0 178.365448 7094.227051 77.90667 1.31488 08-Jan-08 14:25:0 0 179.3854675 7285.911133 77.871292 1.31498



### Page 5 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 14:26:0 0 178.647018 4 7160.72509 8 77.56580 4 1.31509 08-Jan-08 14:27:0 0 177.9085693 7144.88623 77.744896 1.31519 08-Jan-08 14:28:0 0 179.952804 6 7164.19775 4 77.735741 1.31529 08-Jan-08 14:29:0 0 177.9742889 7183.50976 6 77.696289 1.31539 08-Jan-08 14:30:0 0 179.4810333 7160.15625 77.541023 1.31549 08-Jan-08 14:31:0 0 180.138031 7156.5141 6 77.593811 1.31559 08-Jan-08 14:32:0 0 179.9744263 7237.52343 8 77.28833 1.3157 08-Jan-08 14:33:0 0 178.790191 7 7145.024902 77.322639 1.3158 08-Jan-08 14:34:0 0 179.447143 6 7157.181152 77.526848 1.3159 08-Jan-08 14:35:0 0 179.384903 7282.027832 77.731056 1.316 08-Jan-08 14:36:0 0 179.247558 6 7189.54589 8 77.71957 4 1.3161 08-Jan-08 14:37:0 0 179.1102295 7145.910645 77.564316 1.31621 08-Jan-08 14:38:0 0 178.3059082 7132.068359 77.186501 1.31631 08-Jan-08 14:39:0 0 179.376815 8 7140.227051 77.499619 1.31641 08-Jan-08 14:40:0 0 179.2567291 7126.599121 77.817871 1.31651 08-Jan-08 14:41:0 0 178.796966 6 7127.414063 78.033463 1.31661 08-Jan-08 14:42:0 0 178.923034 7 7137.06982 4 77.848671 1.31672 08-Jan-08 14:43:0 0 179.687484 7 7146.72558 6 77.663879 1.31682 08-Jan-08 14:44:0 0 179.148315 4 7141.81640 6 77.479088 1.31692 08-Jan-08 14:45:0 0 178.025787 4 7127.05761 7 77.294296 1.31702 08-Jan-08 14:46:0 0 178.5913391 7121.19677 7 77.443153 1.31712 08-Jan-08 14:47:0 0 179.227401 7 7122.45214 8 77.812737 1.31723 08-Jan-08 14:48:0 0 179.094070 4 7131.243652 77.499619 1.31733 08-Jan-08 14:49:0 0 179.7062683 7163.019531 77.499619 1.31743 08-Jan-08 14:50:0 0 179.775695 8 7279.377441 77.287506 1.31753 08-Jan-08 14:51:0 0 179.568573 7195.23388 7 76.90588 4 1.31763 08-Jan-08 14:52:0 0 178.789596 6 7121.3125 77.008553 1.31773 08-Jan-08 14:53:0 0 178.4000092 7086.710449 77.11121 4 1.31784 08-Jan-08 14:54:0 0 178.6108093 7126.19043 77.019501 1.31794 08-Jan-08 14:55:0 0 179.191848 8 7141.040039 76.64106 1.31804 08-Jan-08 14:56:0 0 178.9859161 7152.77392 6 76.80151 4 1.31814 08-Jan-08 14:57:0 0 178.788253 8 7134.109863 76.49353 1.31824 08-Jan-08 14:58:0 0 178.599136 4 7110.092285 76.309761 1.31835 08-Jan-08 14:59:0 0 178.4100342 7130.724121 76.529205 1.31845 08-Jan-08 15:00:0 0 178.046798 7 7096.57373 76.3739 4 1.31855 08-Jan-08 15:01:0 0 178.8302765 7108.55224 6 76.322838 1.31865 08-Jan-08 15:02:0 0 179.4929962 7188.587402 76.735741 1.31875 08-Jan-08 15:03:0 0 179.850280 8 7189.879883 77.148651 1.31886 08-Jan-08 15:04:0 0 179.8636475 7203.93066 4 77.590523 1.31896 08-Jan-08 15:05:0 0 178.8659363 7276.013672 78.089928 1.31906 08-Jan-08 15:06:0 0 178.772857 7 7180.467285 77.828262 1.31916 08-Jan-08 15:07:0 0 178.2908783 7149.36377 77.983528 1.31926 08-Jan-08 15:08:0 0 178.6470032 7155.499512 78.13879 4 1.31937 08-Jan-08 15:09:0 0 178.454269 4 7132.386719 78.294067 1.31947 08-Jan-08 15:10:0 0 179.525695 8 7166.23095 7 78.129967 1.31957



### Page 6 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 15:11:0 0 179.720779 4 7205.257813 78.253166 1.31967 08-Jan-08 15:12:0 0 179.2569885 7203.70556 6 78.376358 1.31977 08-Jan-08 15:13:0 0 179.2663422 7143.266113 78.49955 1.31988 08-Jan-08 15:14:0 0 177.9451141 7135.35693 4 78.622742 1.31998 08-Jan-08 15:15:0 0 178.4899139 7232.729492 78.745941 1.32008 08-Jan-08 15:16:0 0 179.0346985 7164.57275 4 78.51955 4 1.32018 08-Jan-08 15:17:0 0 179.785461 4 7148.15966 8 78.274765 1.32028 08-Jan-08 15:18:0 0 177.984069 8 7102.966309 78.02998 4 1.32038 08-Jan-08 15:19:0 0 178.2372589 7098.60302 7 77.785202 1.32049 08-Jan-08 15:20:0 0 178.529937 7 7108.87011 7 77.540413 1.32059 08-Jan-08 15:21:0 0 179.3815613 7121.13525 4 77.499619 1.32069 08-Jan-08 15:22:0 0 179.853088 4 7165.668945 77.557022 1.32079 08-Jan-08 15:23:0 0 178.1047363 7104.63476 6 77.562241 1.32089 08-Jan-08 15:24:0 0 178.4437103 7100.3266 6 77.266479 1.321 08-Jan-08 15:25:0 0 179.9899292 7170.34423 8 77.36858 4 1.3211 08-Jan-08 15:26:0 0 179.2054443 7155.121582 77.470688 1.3212 08-Jan-08 15:27:0 0 178.56987 7169.01757 8 76.837448 1.3213 08-Jan-08 15:28:0 0 179.009826 7 7173.78466 8 76.506577 1.3214 08-Jan-08 15:29:0 0 179.917846 7 7182.536133 76.429901 1.32151 08-Jan-08 15:30:0 0 179.9994965 7257.09423 8 76.353218 1.32161 08-Jan-08 15:31:0 0 178.741134 6 7188.22216 8 76.276535 1.32171 08-Jan-08 15:32:0 0 178.9490509 7152.499023 76.532028 1.32181 08-Jan-08 15:33:0 0 178.6989899 7140.15429 7 76.994011 1.32191 08-Jan-08 15:34:0 0 178.1134491 7127.809082 77.050812 1.32202 08-Jan-08 15:35:0 0 178.428634 6 7166.164063 76.788681 1.32212 08-Jan-08 15:36:0 0 178.9046021 7173.570801 76.634689 1.32222 08-Jan-08 15:37:0 0 179.133880 6 7157.57470 7 76.71809 4 1.32232 08-Jan-08 15:38:0 0 178.882110 6 7138.69043 77.023575 1.32242 08-Jan-08 15:39:0 0 178.130249 7138.974609 76.899048 1.32253 08-Jan-08 15:40:0 0 177.2048035 7095.88964 8 76.514313 1.32263 08-Jan-08 15:41:0 0 177.251922 6 7074.164063 76.412209 1.32273 08-Jan-08 15:42:0 0 177.833313 7147.530273 76.31010 4 1.32283 08-Jan-08 15:43:0 0 177.810989 4 7090.80224 6 76.364563 1.32293 08-Jan-08 15:44:0 0 178.1754303 7125.453125 76.670876 1.32303 08-Jan-08 15:45:0 0 179.5802765 7225.56591 8 76.977188 1.32314 08-Jan-08 15:46:0 0 179.966735 8 7217.967285 77.088966 1.32324 08-Jan-08 15:47:0 0 179.958648 7 7186.010742 76.967316 1.32334 08-Jan-08 15:48:0 0 179.3937225 7154.05468 8 76.873375 1.32344 08-Jan-08 15:49:0 0 178.99823 7127.36377 77.186501 1.32354 08-Jan-08 15:50:0 0 179.0923309 7127 77.186501 1.32365 08-Jan-08 15:51:0 0 178.146759 7118.93554 7 77.186501 1.32375 08-Jan-08 15:52:0 0 177.437973 7071.743652 77.186501 1.32385 08-Jan-08 15:53:0 0 176.8746033 7056.49023 4 77.480896 1.32395 08-Jan-08 15:54:0 0 177.934845 7084.81591 8 77.378792 1.32405 08-Jan-08 15:55:0 0 177.0437469 7205.710449 77.276688 1.32416



### Page 7 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 15:56:0 0 177.4345703 7103.956543 77.174583 1.32426 08-Jan-08 15:57:0 0 177.0386353 7041.13232 4 77.072479 1.32436 08-Jan-08 15:58:0 0 178.0343781 7040.35009 8 76.970375 1.32446 08-Jan-08 15:59:0 0 178.069549 6 7067.94970 7 76.88903 1.32456 08-Jan-08 16:00:0 0 178.5622711 7083.074219 77.176292 1.32467 08-Jan-08 16:01:0 0 178.7369232 7096.25341 8 76.972076 1.32477 08-Jan-08 16:02:0 0 178.4115295 7111.598145 76.767868 1.32487 08-Jan-08 16:03:0 0 178.9309082 7106.547852 76.56366 1.32497 08-Jan-08 16:04:0 0 179.0524902 7094.08056 6 76.661209 1.32507 08-Jan-08 16:05:0 0 179.1412659 7098.554199 76.76387 1.32518 08-Jan-08 16:06:0 0 177.295150 8 7070.466309 76.866531 1.32528 08-Jan-08 16:07:0 0 177.5951691 7101.169922 77.473526 1.32538 08-Jan-08 16:08:0 0 178.3530731 7106.20556 6 77.186501 1.32548 08-Jan-08 16:09:0 0 179.1670685 7105.71679 7 76.736221 1.32558 08-Jan-08 16:10:0 0 178.4266205 7235.036621 76.580956 1.32568 08-Jan-08 16:11:0 0 178.464309 7 7138.14941 4 76.873375 1.32579 08-Jan-08 16:12:0 0 177.071502 7 7092.974609 76.873375 1.32589 08-Jan-08 16:13:0 0 176.9838562 7089.77636 7 76.873375 1.32599 08-Jan-08 16:14:0 0 177.4191132 7104.62890 6 76.873375 1.32609 08-Jan-08 16:15:0 0 179.037246 7 7181.97802 7 76.873375 1.32619 08-Jan-08 16:16:0 0 179.1507111 7174.92138 7 76.329269 1.3263 08-Jan-08 16:17:0 0 178.6657715 7160.987305 76.614151 1.3264 08-Jan-08 16:18:0 0 179.330230 7 7164.393555 76.691147 1.3265 08-Jan-08 16:19:0 0 178.0054932 7169.03808 6 76.76815 1.3266 08-Jan-08 16:20:0 0 177.5633392 7173.68261 7 76.845146 1.3267 08-Jan-08 16:21:0 0 176.7914429 7133.968262 76.483261 1.32681 08-Jan-08 16:22:0 0 176.825164 8 7179.199219 76.437065 1.32691 08-Jan-08 16:23:0 0 177.1393433 7146.50976 6 76.69072 1.32701 08-Jan-08 16:24:0 0 177.753067 7141.522949 76.81488 1.32711 08-Jan-08 16:25:0 0 177.075866 7 7278.25732 4 76.711655 1.32721 08-Jan-08 16:26:0 0 176.274292 7147.678711 76.608429 1.32732 08-Jan-08 16:27:0 0 176.684478 8 7065.57763 7 76.353226 1.32742 08-Jan-08 16:28:0 0 177.5896149 7079.87793 76.558548 1.32752 08-Jan-08 16:29:0 0 176.9016113 7067.655273 76.76387 1.32762 08-Jan-08 16:30:0 0 176.5413971 7057.38818 4 76.728462 1.32772 08-Jan-08 16:31:0 0 176.963775 6 7072.17773 4 76.417931 1.32782 08-Jan-08 16:32:0 0 177.42152 4 7116.875 76.49556 1.32793 08-Jan-08 16:33:0 0 176.526825 7039.98925 8 76.340302 1.32803 08-Jan-08 16:34:0 0 176.48472 6 7053.07568 4 76.53672 1.32813 08-Jan-08 16:35:0 0 177.3074493 7163.32959 76.475327 1.32823 08-Jan-08 16:36:0 0 177.0774841 7112.060059 76.413933 1.32833 08-Jan-08 16:37:0 0 177.522674 6 7097.436035 76.352531 1.32844 08-Jan-08 16:38:0 0 177.4752045 7078.484375 76.291138 1.32854 08-Jan-08 16:39:0 0 177.297088 6 7074.495605 76.33440 4 1.32864 08-Jan-08 16:40:0 0 176.4541931 7083.15332 76.642387 1.32874



### Page 8 of 9

### Plant Information Database Query Results

Ta g Name: 1pwr j i900 1TSYFI100 1tmsti922m 1tsyai202 Ta g Explanation: Unit Load Fuel Flow Inlet Temp Satuator Ta g Units: Mwe KCFH oF % H2O

A vera g e: 178.6 7124.9 76.7 1.3 08-Jan-08 16:41:0 0 176.87623 6 7093.42041 76.822601 1.32884 08-Jan-08 16:42:0 0 177.5938263 7064.28173 8 76.619499 1.32895 08-Jan-08 16:43:0 0 176.8300171 7078.337891 76.416389 1.32905 08-Jan-08 16:44:0 0 176.249160 8 7030.69384 8 76.29932 4 1.32915 08-Jan-08 16:45:0 0 175.8907471 7037.02050 8 76.53500 4 1.32925 08-Jan-08 16:46:0 0 176.3048401 7053.290039 76.383499 1.32935 08-Jan-08 16:47:0 0 175.7822571 7098.26709 76.26260 4 1.32946 08-Jan-08 16:48:0 0 176.0436401 7027.65332 76.417229 1.32956 08-Jan-08 16:49:0 0 176.217651 4 7063.03808 6 76.57185 4 1.32966 08-Jan-08 16:50:0 0 175.654403 7 7092.240723 76.726479 1.32976 08-Jan-08 16:51:0 0 175.631698 6 7072.36425 8 76.565392 1.32986 08-Jan-08 16:52:0 0 174.923858 6 6997.057129 76.719383 1.32997 08-Jan-08 16:53:0 0 175.419906 6 7027.973145 76.873375 1.33007 08-Jan-08 16:54:0 0 176.853881 8 7044.82959 76.570358 1.33017 08-Jan-08 16:55:0 0 176.745803 8 7062.82714 8 76.707909 1.33027 08-Jan-08 16:56:0 0 175.3784332 7050.512695 76.860649 1.33037 08-Jan-08 16:57:0 0 175.3651581 7037.77050 8 76.767723 1.33047 08-Jan-08 16:58:0 0 176.301101 7 7071.046875 76.652466 1.33058 08-Jan-08 16:59:0 0 175.7945099 7025.039063 76.537209 1.33068 08-Jan-08 17:00:0 0 176.395202 6 7077.90966 8 76.42194 4 1.33078



### Page 9 of 9

## APPENDIX C

FUEL ANALYSISCoal Derived Gas Heatin g Value Calculations Customer: Tampa Electric Company Sample ID: PPS -001 Facility: Polk Power Station Analysis Date: 01/08/2008 Source: Unit 1

CALCULATION OF DENSITY AND HEATING VALUE @ 68°F and 29.92 in H g % volume Component Gross Volume % Molecular Density x Gross Weight Heating Value Fract. Component Volume Wt. (lb/ft 3 ) Density weight % Btu/lb Fract. Btu (Btu/SCF) Btu Hydrogen 33.4600 2.016 0.00524 0.00175 3.0318 61000.2 1849.42 319.5 106.915 Oxygen 0.0000 31.999 0.08314 0.00000 0.0000 0 0.00 0.0 0 Argon 0.7000 39.948 0.10380 0.00073 1.2568 0 0.00 0.0 0 Nitrogen 3.2800 28.014 0.07279 0.00239 4.1299 0 0.00 0.0 0 CO2 18.1100 44.010 0.11435 0.02071 35.8227 0 0.00 0.0 0 CO 44.2700 28.010 0.07278 0.03222 55.7328 4339.8 2418.69 315.8 139.825 COS 0.0000 60.070 0.15608 0.00000 0.0000 0 0.00 0.0 0 Methane 0.0361 16.043 0.04168 0.00002 0.0260 23911.2 6.22 996.7 0.35982 Total: 99.86 Total Densit y 0.05781 100.0000 Gross Heating Value Specific Gravit y 0.75569 Btu/lb 4274 Btu/SCF 247.10 Net Heating Values Btu/lb 3995 Btu/SCF 231

Net Heating Value (Lower Heating Value), Btu/lb, calculated as Gross Heating Value (Higher Heating Value) - 10.30 (%H 2 x 8.9 4

CALCULATION OF F FACTORS Weight Percents Componen t Mol. Wt. C Factor H Factor % volume Fract. Wt. Carbon Hydrogen Nitrogen Oxygen Hydrogen 2.016 0 1 33.460 67.4554 3.0318272 Oxygen 31.999 0 0 0.000 0.0000 0 Argon 39.948 0 0 0.700 27.9636 Nitrogen 28.014 0 0 3.280 91.8859 4.129875344 CO2 44.010 0.27291525 0 18.110 797.0211 9.77654925 26.0431 CO 28.010 0.42881114 0 44.270 1240.0027 23.8988313 32.0296 COS 60.070 0.19995006 0 0.000 0.0000 0 0 Methane 16.043 0.74867543 0.251325 0.036 0.5792 0.01948832 0.0065421

Totals 99.85610 2224.9078 33.6948689 3.04 4.129875344 58.0727 CALCULATED VALUES O2 F Factor (dry), Fd 8534 DSCF of Exhaust/MM Btu of Fuel Burned @ 0% excess air Predicted Fo Factor 0.70 EPA Method 3a Fo value

## APPENDIX D

CEMS DATA

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 10:46 38.34 17.6 10.8 827.7 01/08/2008 10:47 38.23 17.6 10.8 829.9 01/08/2008 10:48 37.99 17.6 10.8 822.6 01/08/2008 10:49 37.91 17.4 10.8 842 01/08/2008 10:50 38.22 17.5 10.8 834.7 01/08/2008 10:51 39.05 16.8 10.7 832.2 01/08/2008 10:52 37.92 16.6 10.7 843.2 01/08/2008 10:53 37.76 17.5 10.8 821 01/08/2008 10:54 38.59 17.5 10.8 827 01/08/2008 10:55 38.53 17.6 10.8 819.4 01/08/2008 10:56 38.57 17.8 10.8 842 01/08/2008 10:57 38.53 17.6 10.8 841 01/08/2008 10:58 38.67 17.5 10.7 841.4 01/08/2008 10:59 39.01 17.5 10.8 848.6 01/08/2008 11:00 38.77 17.6 10.8 851.9 01/08/2008 11:01 38.44 17.9 10.8 832.5 01/08/2008 11:02 38.56 17.8 10.8 845.6 01/08/2008 11:03 38.89 17.6 10.7 828.7 01/08/2008 11:04 38.6 17.3 10.7 837.4 01/08/2008 11:05 38.94 17.1 10.7 839.4 01/08/2008 11:06 39.31 16.8 10.7 843.8 01/08/2008 11:07 38.21 16.5 10.7 862.8 01/08/2008 11:08 37.92 16.8 10.7 843 01/08/2008 11:09 38.58 16.8 10.7 844.2 01/08/2008 11:10 38.67 17 10.7 846.8 01/08/2008 11:11 38.43 17 10.7 852.1 01/08/2008 11:12 38.44 16.8 10.7 848.1 01/08/2008 11:13 38.62 16.9 10.7 839.3 01/08/2008 11:14 39.07 16.6 10.7 847 01/08/2008 11:15 39.7 16.8 10.7 843 01/08/2008 11:16 40.01 16.4 10.6 838.5 01/08/2008 11:17 38.89 16.1 10.7 834.3 01/08/2008 11:18 38.85 17.1 10.7 812 01/08/2008 11:19 39.2 17.3 10.7 838.6 01/08/2008 11:20 39.28 17.1 10.7 848.5 01/08/2008 11:21 39.47 17.2 10.7 844.5 01/08/2008 11:22 39.13 17.4 10.7 858.7 01/08/2008 11:23 38.82 17.5 10.7 833.7 01/08/2008 11:24 38.82 17.4 10.7 839.4 01/08/2008 11:25 38.71 17.3 10.7 846.4

Page 1 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 11:26 38.92 17.6 10.8 839.8 01/08/2008 11:27 38.72 17.6 10.8 843.9 01/08/2008 11:28 38.37 17.3 10.8 851.1 01/08/2008 11:29 38.56 17.7 10.7 837.4 01/08/2008 11:30 38.82 17.1 10.7 844.4 01/08/2008 11:31 39.44 16.4 10.7 850.7 01/08/2008 11:32 38.04 16.6 10.7 841.4 01/08/2008 11:33 37.89 17.3 10.7 855 01/08/2008 11:34 38.42 17.1 10.7 860.6 01/08/2008 11:35 38.63 17.2 10.7 832.7 01/08/2008 11:36 38.25 17.1 10.7 828.6 01/08/2008 11:37 38.69 16.9 10.7 835.9 01/08/2008 11:38 39.12 17 10.8 836.1 01/08/2008 11:39 39.13 17.3 10.8 844.6 01/08/2008 11:40 39.38 17.4 10.7 844.4 01/08/2008 11:41 39.38 17.5 10.7 848.4 01/08/2008 11:42 39.11 17.5 10.7 842.5 01/08/2008 11:43 38.69 17.3 10.7 842.4 01/08/2008 11:44 38.6 17.3 10.7 841 01/08/2008 11:45 38.61 17.5 10.8 837.3 01/08/2008 11:46 39.1 17.2 10.7 838.3 01/08/2008 11:47 37.92 16.7 10.7 836.9 01/08/2008 11:48 37.53 17.2 10.8 849.9 01/08/2008 11:49 37.81 17.5 10.8 838.6 01/08/2008 11:50 38.32 17.5 10.8 835.9 01/08/2008 11:51 38.57 17.2 10.7 818.7 01/08/2008 11:52 38.97 16.9 10.8 826.8 01/08/2008 11:53 38.8 17.3 10.8 852.9 01/08/2008 11:54 39.21 17.2 10.8 840.1 01/08/2008 11:55 39.28 17.5 10.8 837.4 01/08/2008 11:56 39.69 17 10.7 825.1 01/08/2008 11:57 38.74 16.8 10.7 833.6 01/08/2008 11:58 38.1 17.5 10.8 848.9 01/08/2008 11:59 38.63 17.5 10.7 849 01/08/2008 12:00 38.77 17.3 10.7 838.5 01/08/2008 12:01 38.81 17.2 10.7 830.3 01/08/2008 12:02 38.5 16.9 10.7 842.3 01/08/2008 12:03 38.64 17.1 10.8 845.3 01/08/2008 12:04 39.11 17.2 10.7 840.8 01/08/2008 12:05 38.8 17.4 10.8 864.7

Page 2 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 12:06 39.17 17.3 10.8 850.8 01/08/2008 12:07 39.31 17.3 10.8 846.9 01/08/2008 12:08 39.22 17.3 10.7 830.6 01/08/2008 12:09 39.22 17 10.7 845.6 01/08/2008 12:10 39.68 17 10.7 863.5 01/08/2008 12:11 39.83 16.7 10.7 835.6 01/08/2008 12:12 38.42 16.7 10.7 833.7 01/08/2008 12:13 38.16 17.3 10.8 827.9 01/08/2008 12:14 38.85 17.3 10.8 842.8 01/08/2008 12:15 38.82 17.1 10.8 844.5 01/08/2008 12:16 38.77 17.4 10.7 850.4 01/08/2008 12:17 38.99 17.1 10.8 835.9 01/08/2008 12:18 38.99 17.5 10.8 859.3 01/08/2008 12:19 38.96 17.6 10.8 841.9 01/08/2008 12:20 39.06 17.6 10.7 845.4 01/08/2008 12:21 39.03 17.1 10.7 833 01/08/2008 12:22 38.87 16.9 10.7 851.8 01/08/2008 12:23 38.85 16.7 10.7 813.8 01/08/2008 12:24 39.17 16.8 10.7 830.4 01/08/2008 12:25 39.61 17 10.7 836.5 01/08/2008 12:26 36.76 12.8 10.6 847.8 01/08/2008 12:27 6.89 0.4 10.7 851.3 01/08/2008 12:28 16.8 10.2 10.7 840.3 01/08/2008 12:29 36.9 16.3 10.7 833.5 01/08/2008 12:30 38.52 16.4 10.7 830.5 01/08/2008 12:31 38.82 16.1 10.7 832.3 01/08/2008 12:32 39.09 16.2 10.7 830.3 01/08/2008 12:33 38.96 16.5 10.7 829.4 01/08/2008 12:34 39.27 16.7 10.7 836.6 01/08/2008 12:35 39.5 16.7 10.7 837.9 01/08/2008 12:36 40.3 16.2 10.6 849.7 01/08/2008 12:37 39.46 16.1 10.7 843 01/08/2008 12:38 38.8 16.8 10.8 826.6 01/08/2008 12:39 39.1 17.1 10.8 836.2 01/08/2008 12:40 39.03 17.5 10.8 845.4 01/08/2008 12:41 38.76 17.1 10.7 850 01/08/2008 12:42 38.34 17 10.7 825.4 01/08/2008 12:43 37.78 17 10.8 783.5 01/08/2008 12:44 38.09 17.2 10.8 807 01/08/2008 12:45 37.67 17.5 10.8 822.4

Page 3 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 12:46 38.03 17.5 10.8 832 01/08/2008 12:47 38.06 17.3 10.8 840.5 01/08/2008 12:48 38.41 17.1 10.8 829.9 01/08/2008 12:49 38.1 17.1 10.8 836.5 01/08/2008 12:50 38.75 17.2 10.8 834.8 01/08/2008 12:51 39.23 16.7 10.7 825.5 01/08/2008 12:52 38.45 16.6 10.8 832.5 01/08/2008 12:53 37.97 17.3 10.8 841.4 01/08/2008 12:54 38.47 17.3 10.8 843 01/08/2008 12:55 38.68 17.3 10.8 845.4 01/08/2008 12:56 38.73 17.2 10.8 844.3 01/08/2008 12:57 38.55 17.3 10.8 836.3 01/08/2008 12:58 38.78 17.4 10.8 844.2 01/08/2008 12:59 38.56 17.4 10.8 860.4 01/08/2008 13:00 38.93 17.3 10.8 832.5 01/08/2008 13:01 38.69 17.7 10.8 837.7 01/08/2008 13:02 38.57 17.6 10.8 837 01/08/2008 13:03 38.42 17.8 10.8 854.2 01/08/2008 13:04 38.64 17.5 10.8 843.4 01/08/2008 13:05 38.3 17.5 10.8 849 01/08/2008 13:06 39.1 17 10.7 846.6 01/08/2008 13:07 38.13 16.5 10.8 838.8 01/08/2008 13:08 37.28 17.4 10.8 830.4 01/08/2008 13:09 37.17 17.6 10.8 828.3 01/08/2008 13:10 37.77 17.9 10.8 824.7 01/08/2008 13:11 37.72 17.8 10.8 827.1 01/08/2008 13:12 38.47 17.6 10.8 848.9 01/08/2008 13:13 38.22 17.5 10.8 840.1 01/08/2008 13:14 38.46 17.6 10.8 825.8 01/08/2008 13:15 38.28 17.6 10.8 836.9 01/08/2008 13:16 39 17.6 10.8 838.3 01/08/2008 13:17 38.26 17.1 10.8 844.8 01/08/2008 13:18 38.05 17.9 10.8 836.1 01/08/2008 13:19 38.49 17.5 10.8 852.5 01/08/2008 13:20 38.54 17.5 10.8 826.8 01/08/2008 13:21 38.42 17.6 10.8 824.3 01/08/2008 13:22 38.75 17.7 10.8 852.2 01/08/2008 13:23 38.47 17.8 10.8 863.8 01/08/2008 13:24 38.7 17.7 10.8 839 01/08/2008 13:25 38.3 17.2 10.8 834.5

Page 4 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 13:26 38.68 17.3 10.8 836.3 01/08/2008 13:27 38.16 17.2 10.8 838.5 01/08/2008 13:28 38.2 17.5 10.8 844.7 01/08/2008 13:29 38.35 17.5 10.8 800.8 01/08/2008 13:30 38.43 17.7 10.8 837.1 01/08/2008 13:31 39.03 17.1 10.7 825.2 01/08/2008 13:32 38.22 16.5 10.8 852.3 01/08/2008 13:33 37.85 17 10.8 863.4 01/08/2008 13:34 38.27 17.3 10.8 830.5 01/08/2008 13:35 37.9 17.4 10.8 836.8 01/08/2008 13:36 38.12 17.5 10.8 837.5 01/08/2008 13:37 38.21 17.6 10.8 844 01/08/2008 13:38 38.32 17.7 10.8 844 01/08/2008 13:39 38.37 17.4 10.8 822.3 01/08/2008 13:40 38.66 17.4 10.8 833 01/08/2008 13:41 38.77 17.3 10.8 828.4 01/08/2008 13:42 38.63 17.3 10.8 839.1 01/08/2008 13:43 38.71 17.2 10.7 846.1 01/08/2008 13:44 39.17 17 10.7 843 01/08/2008 13:45 39 17 10.7 842.9 01/08/2008 13:46 39.82 16.8 10.7 814.3 01/08/2008 13:47 38.69 16.2 10.7 853.6 01/08/2008 13:48 38.29 16.7 10.7 850.1 01/08/2008 13:49 39.01 16.6 10.7 845.6 01/08/2008 13:50 39.3 16.6 10.7 843.8 01/08/2008 13:51 39.14 16.8 10.7 842.7 01/08/2008 13:52 39.33 16.8 10.7 852.2 01/08/2008 13:53 39.4 16.8 10.8 825.7 01/08/2008 13:54 40.04 16.9 10.8 839.8 01/08/2008 13:55 40.29 17.1 10.8 842.3 01/08/2008 13:56 41.06 16.9 10.7 842.6 01/08/2008 13:57 39.72 16.7 10.8 832.8 01/08/2008 13:58 38.97 17.5 10.8 834.1 01/08/2008 13:59 39.95 17.6 10.8 822.3 01/08/2008 14:00 39.59 17.5 10.8 838.8 01/08/2008 14:01 39.4 17.5 10.8 839.3 01/08/2008 14:02 39.17 17.2 10.8 850.2 01/08/2008 14:03 38.83 17.4 10.8 841.3 01/08/2008 14:04 38.75 17.6 10.8 822.3 01/08/2008 14:05 38.73 17.9 10.8 830.6

Page 5 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 14:06 39.04 17.6 10.8 845.2 01/08/2008 14:07 39.16 17.4 10.8 842.9 01/08/2008 14:08 39.59 17.4 10.8 811.1 01/08/2008 14:09 39.06 17.4 10.8 825.7 01/08/2008 14:10 39.74 17.3 10.8 843.7 01/08/2008 14:11 40.66 17 10.7 839.1 01/08/2008 14:12 39.63 16.2 10.8 845 01/08/2008 14:13 38.85 17 10.8 841.8 01/08/2008 14:14 39.29 17.4 10.8 861.2 01/08/2008 14:15 39.51 17.6 10.8 843.6 01/08/2008 14:16 39.59 17.8 10.8 828.9 01/08/2008 14:17 39.89 17.4 10.8 834.8 01/08/2008 14:18 40.03 17.2 10.8 830.3 01/08/2008 14:19 40.31 17.5 10.8 847.1 01/08/2008 14:20 40.15 17.5 10.8 838.3 01/08/2008 14:21 40.38 17.8 10.8 830.4 01/08/2008 14:22 39.94 17.6 10.8 852 01/08/2008 14:23 39.59 17.7 10.8 848.9 01/08/2008 14:24 39.84 17.5 10.8 839.9 01/08/2008 14:25 39.69 17.4 10.8 831.1 01/08/2008 14:26 39.95 17.2 10.7 827.4 01/08/2008 14:27 38.73 16.6 10.8 844 01/08/2008 14:28 37.77 17.1 10.8 854.1 01/08/2008 14:29 38.53 17.5 10.8 858 01/08/2008 14:30 38.63 17.6 10.8 847.8 01/08/2008 14:31 38.82 17.5 10.8 834.2 01/08/2008 14:32 38.91 17 10.8 831.4 01/08/2008 14:33 39.28 17.3 10.8 847 01/08/2008 14:34 39.73 17.3 10.8 835.9 01/08/2008 14:35 40 16.9 10.8 852 01/08/2008 14:36 40.91 16.9 10.7 831.5 01/08/2008 14:37 40.27 16.3 10.8 826.1 01/08/2008 14:38 39.58 17.3 10.8 843.9 01/08/2008 14:39 39.46 17.4 10.8 847 01/08/2008 14:40 40.06 17.5 10.8 834.2 01/08/2008 14:41 40 17.3 10.8 836.4 01/08/2008 14:42 39.5 17.1 10.8 858.7 01/08/2008 14:43 39.27 17.3 10.8 832.3 01/08/2008 14:44 39.25 17.6 10.8 845.6 01/08/2008 14:45 39.01 17.5 10.8 821.9

Page 6 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 14:46 38.92 17.2 10.8 830.5 01/08/2008 14:47 39.02 17 10.8 842.9 01/08/2008 14:48 38.88 17.2 10.8 831.5 01/08/2008 14:49 38.82 17.3 10.8 833.9 01/08/2008 14:50 38.85 17.2 10.8 832.2 01/08/2008 14:51 39.62 17.3 10.7 843.5 01/08/2008 14:52 38.78 16.7 10.8 816.4 01/08/2008 14:53 38.18 17.4 10.8 831.3 01/08/2008 14:54 38.94 17.1 10.8 827.7 01/08/2008 14:55 39.11 17.2 10.8 846.4 01/08/2008 14:56 38.9 17.2 10.8 841.9 01/08/2008 14:57 39.23 16.9 10.7 849.5 01/08/2008 14:58 39.16 17 10.7 850.7 01/08/2008 14:59 39.39 17 10.7 852.5 01/08/2008 15:00 39.49 17 10.7 856.8 01/08/2008 15:01 39.56 16.8 10.7 849.7 01/08/2008 15:02 39.06 16.8 10.7 858.2 01/08/2008 15:03 38.96 17 10.7 822.9 01/08/2008 15:04 38.39 17.1 10.7 861 01/08/2008 15:05 38.85 16.8 10.7 866.3 01/08/2008 15:06 39.4 16.4 10.6 847.9 01/08/2008 15:07 38.53 15.8 10.7 849 01/08/2008 15:08 37.97 16.4 10.7 830.7 01/08/2008 15:09 38.36 16.6 10.7 857.9 01/08/2008 15:10 38.78 16.7 10.8 876.1 01/08/2008 15:11 38.94 16.8 10.7 868.6 01/08/2008 15:12 39.42 17 10.8 863.7 01/08/2008 15:13 39.24 17.2 10.8 868.1 01/08/2008 15:14 39.58 17.2 10.8 845.1 01/08/2008 15:15 39.76 17.1 10.8 859.5 01/08/2008 15:16 40.01 16.8 10.7 843.6 01/08/2008 15:17 39.16 16.3 10.8 813.8 01/08/2008 15:18 38.14 17.2 10.8 811.4 01/08/2008 15:19 38.29 17.4 10.8 835 01/08/2008 15:20 38.45 17 10.8 824.3 01/08/2008 15:21 38.69 16.9 10.7 839.2 01/08/2008 15:22 38.19 16.8 10.8 808.2 01/08/2008 15:23 38.02 17.2 10.8 827.2 01/08/2008 15:24 37.63 17.5 10.8 850.6 01/08/2008 15:25 38.05 17.1 10.8 853.3

Page 7 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 15:26 38.27 17.3 10.8 847.3 01/08/2008 15:27 37.75 17.3 10.8 851.9 01/08/2008 15:28 37.59 17.2 10.7 844.1 01/08/2008 15:29 37.85 16.9 10.8 839.2 01/08/2008 15:30 38.34 17 10.8 846.1 01/08/2008 15:31 38.98 16.9 10.7 859 01/08/2008 15:32 38.61 16.1 10.7 859.8 01/08/2008 15:33 38.03 16.7 10.7 855.1 01/08/2008 15:34 38.91 16.7 10.7 853.1 01/08/2008 15:35 39.23 16.6 10.7 858.6 01/08/2008 15:36 39.05 16.5 10.7 857.9 01/08/2008 15:37 38.99 16.4 10.7 853.5 01/08/2008 15:38 38.8 16.7 10.7 837.6 01/08/2008 15:39 39.32 16.8 10.7 834.8 01/08/2008 15:40 39.23 16.7 10.7 836.8 01/08/2008 15:41 39.23 16.6 10.7 836.6 01/08/2008 15:42 38.84 16.3 10.7 834.6 01/08/2008 15:43 38.6 16.4 10.7 829.3 01/08/2008 15:44 38.66 16.4 10.7 837.2 01/08/2008 15:45 38.56 16.6 10.7 851.2 01/08/2008 15:46 38.9 16.6 10.7 827.2 01/08/2008 15:47 37.92 16.1 10.7 830.9 01/08/2008 15:48 37.51 17 10.8 868.5 01/08/2008 15:49 37.98 17.2 10.7 830.7 01/08/2008 15:50 38.56 16.8 10.7 841 01/08/2008 15:51 39.28 16.8 10.7 842.1 01/08/2008 15:52 39.25 16.5 10.8 837.7 01/08/2008 15:53 39.38 16.8 10.8 854.9 01/08/2008 15:54 39.31 16.9 10.8 825.5 01/08/2008 15:55 39.75 17 10.8 822.6 01/08/2008 15:56 40.11 16.9 10.7 817.4 01/08/2008 15:57 39.52 16.3 10.8 832.1 01/08/2008 15:58 38.13 16.9 10.8 820.7 01/08/2008 15:59 38.29 17 10.8 826.9 01/08/2008 16:00 37.72 17.2 10.8 822.9 01/08/2008 16:01 37.51 17.2 10.8 839 01/08/2008 16:02 36.84 17 10.8 856.6 01/08/2008 16:03 36.94 17.3 10.8 853 01/08/2008 16:04 37.13 17.4 10.8 827.1 01/08/2008 16:05 37.53 17.5 10.8 820.3

Page 8 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 16:06 37.28 17.5 10.8 824 01/08/2008 16:07 37.7 17.2 10.8 828.9 01/08/2008 16:08 37.35 17.1 10.8 824.4 01/08/2008 16:09 37.61 17.2 10.8 830.4 01/08/2008 16:10 37.65 17.4 10.8 829.5 01/08/2008 16:11 38.39 17.2 10.7 830.9 01/08/2008 16:12 37.69 16.3 10.8 824.3 01/08/2008 16:13 36.59 16.9 10.8 838.3 01/08/2008 16:14 36.92 16.9 10.8 837.3 01/08/2008 16:15 37.15 16.6 10.7 823.2 01/08/2008 16:16 37.17 16.6 10.7 825.6 01/08/2008 16:17 37.24 16.4 10.7 835.6 01/08/2008 16:18 37.62 16.4 10.7 848.2 01/08/2008 16:19 37.98 16.3 10.7 844 01/08/2008 16:20 38.6 16.5 10.7 828.6 01/08/2008 16:21 38.57 16.3 10.7 814.5 01/08/2008 16:22 39.16 16 10.7 821.6 01/08/2008 16:23 39.37 15.6 10.7 824.7 01/08/2008 16:24 38.93 15.8 10.7 833.5 01/08/2008 16:25 39.05 15.9 10.7 815.4 01/08/2008 16:26 39.86 16.1 10.7 806.3 01/08/2008 16:27 39.64 15.5 10.7 819.7 01/08/2008 16:28 38.14 16.2 10.7 810 01/08/2008 16:29 38.61 16.4 10.7 802.6 01/08/2008 16:30 38.55 16.6 10.7 818.5 01/08/2008 16:31 38.41 16.6 10.7 849.1 01/08/2008 16:32 38.1 16.5 10.7 840 01/08/2008 16:33 37.65 16.6 10.8 838.2 01/08/2008 16:34 36.94 16.9 10.8 832 01/08/2008 16:35 36.76 16.8 10.8 840.9 01/08/2008 16:36 38.07 16.8 10.7 810.4 01/08/2008 16:37 37.33 15.8 10.7 834.3 01/08/2008 16:38 36.31 16.8 10.8 851.9 01/08/2008 16:39 36.55 16.9 10.8 848 01/08/2008 16:40 36.72 16.7 10.8 818.5 01/08/2008 16:41 36.92 16.6 10.7 837.7 01/08/2008 16:42 37.25 16.3 10.7 799.8 01/08/2008 16:43 37.38 16.6 10.7 826.9 01/08/2008 16:44 37.32 16.5 10.8 833.1 01/08/2008 16:45 37.99 16.5 10.7 837.7

Page 9 of 10

### SO2 & NOx CEM Data

Date Time SO21 NOX1 OXY1 FLO1 01/08/2008 16:46 37.91 16.5 10.7 831.5 01/08/2008 16:47 38.08 16.6 10.8 822.2 01/08/2008 16:48 37.47 16.5 10.8 828.9 01/08/2008 16:49 37.45 16.6 10.8 825.2 01/08/2008 16:50 37.36 16.6 10.7 825.6 01/08/2008 16:51 37.95 16.5 10.7 822.3 01/08/2008 16:52 37.37 15.6 10.7 827.4 01/08/2008 16:53 36.37 16.3 10.8 823.1 01/08/2008 16:54 36.53 16.6 10.8 840.9 01/08/2008 16:55 36.8 16.9 10.8 798.7 01/08/2008 16:56 36.51 16.9 10.8 823.1 01/08/2008 16:57 37.03 16.8 10.7 816.6 01/08/2008 16:58 36.96 16.6 10.8 810.3 01/08/2008 16:59 37.09 16.7 10.8 827.4 01/08/2008 17:00 36.73 16.8 10.8 833 A verages: 38.493 16.97 10.76 837.87

Page 10 of 10

## APPENDIX E

VISIBLE EMISSIONS DATA SHEET

## APPENDIX F

TEST PARTICIPANTS

## TEST PARTICIPANTS

AIR SERVICES GROUP TEST TEAM

Jorge Varino Environmental Technician – Team Lead Gary Barber Associate Technician

Scott Given Associate Technician Ryan Newell Associate Technician David A. Smith Coordinator, Air Services Group

PROCESS DATA

Raymond A. McDarby Senior Environmental Technician

FUEL ANALYSIS

Bret Nicholas Lab Team Leader – Polk Power Station Raymond A. McDarby Senior Environmental Technician

REPORT PREPARATION

Raymond A. McDarby Senior Environmental Technician

QUALITY ASSURANCE / QUALITY CONTROL

Raymond A. McDarby Senior Environmental Technician

POLK POWER STATION

Michael Perkins Environmental Coordinator Joshua Ellwein Principal Engineer