# • To: Through: From: Date: 

## MEMORANDUM FILE

- CHEVRON PRODUCTS COMPANY JeffDean, Compliance Manager Harold Burge, Environmental Scientist

# -~ 4/29/2003 Subject: Company: Contractor: Location: Source: AIRS#: AO#: Action Code: Subject: ChevronProducts Company Sherman 

### & Rhodes Environmental 2351 N. 1100W., North SaltLake, Davis Co., Utah FCC CO Boiler 

### & CatalystRegenerator 01100003 DAQE-AN0119046-02 dated 7/1212002 3A 

## Review ofStackTestReportdated 3/1912003 On

### 3/20/2003 DAQreceived a stacktestreportfor theFCC CO Boiler 

### & CatalystRegenerator. Thetest was performed on 112112003 to determine thePMIO' S02' 

### & NOxemission factors that will be used for the facility emission caps over the nextthree years. The DAQ-calculated testresults are: 

# • Source FCC CO Boiler 

### & CatalystRegenerator


## DEVIATIONS: TestDate 112112003

None noted. 

## Pollutant ResultlEmissionFactor 6.51blhr 154.3lblhr 55.11blhr



# • CONCLUSION: RECOMMENDATIONS: The emission factors appearto be acceptable. None.

# •
MEMORANDUM DAQC-435-2007 Site ID

## # 10119-B4 To: Through: From: Date: STACKTEST FILE - CHEVRON SALT LAKE REFINERY 

## HaroldBurge, Major Source Compliance

# Manage~ RobertSirrine, Environmental Scientist March 28,2007 Subject: Company: Contact: Tester: Location: Sources: AIRS#: Permit#: 

## Action Code: Subject: Chevron SaltLake Refinery Kris Battleson (801-539-7222) 

## AirPollutionTesting 2351 North 1100West, SaltLake City, SaltLake Co., UT FCC CO Boilerand RegeneratorVent 01100003 DAQE-ANOI19064-06 DatedJuly 14,2006 TR Review ofStackTestReports Received 03/1212007 

## On 03/1212007

## DAQ received Chevron's stack test report for the FCC CO Boiler and Regenerator Vent. Testing was performed to determine the FCC CO Boiler & 

## Regenerator emission factors for the CAP limits found in Conditions 8, 18, & 

## 20 ofthe AO DAQE-ANOI19064-06 DatedJuly 14,2006 The DAQcalculatedtestresults are: Source 

## FCC CO Boiler & 

## Regenerator Test Date 

## 11/1512006 Pollutant 

## PM10 

## Result 

## 19.01bslhr Limit 

## forEmission Cap NOx 106.4 lbslhr forEmission Cap S02 5.61bslhr forEmission Cap DEVIATIONS: 

## None noted. CONCLUSION: 

## At the time of testing, emissions appeared to have been accurately measured. CURRENT RECOMMENDATIONS: 

## Theemission factors shouldbe accepted as accurate. AITACHMENTS: 1 DAQ TestReview Forms 2E-mail from Chevron detailing the productionrate and coke rate

. 3 Chevron FCC CO Boiler & 

## RegeneratorVent StackTestReport ReceivedMarch 12,2007

INSPECTOR'S SIGNATURE:

## StackTests - Selected Companies 

# IChevron Products Company

Address: P.O Box 25117 Salt Lake City UT 84125 Source Contact: Salutation: Phone: L.R. Shanks Mr. (801) 539-7200 Source: Comments:

AO DAQE: OPNo.: Amine Plant Fuel Gas Line 12/30/92 test was conducted to determine the relative accuracyof theirApplyed Audomation AV4850 H2S monitor.
AO Date: OP Date: AIRS No.: Location: Uintah Size: A NSPS Subpart: 11/27/1991 4700021

Method Limitation Last Test Result Test Due Period Comments 11 H2S 11 H2S Source: 0.10 gr/dscf 160 ppm BulkTerminal VRU Rack 12/30/1992 0.038 gr/dscf 64.35 ppmdy AIRS No.: 3500240 RATA

Comments:

AO DAQE: OPNo.: DAQE-144-00, DATED 3/13/00, CHANGED SOURCE TESTING TO CEM.

AO Date: OP Date: Location: Salt Lake Size: A NSPS Subpart: 1/19/1994

Method 25B 25B 25B Source: Limitation .08 Ibs/1000 gal

Cat Reformer LastTest 4/29/1993 5/13/1992 12/28/1987 Result .000465/1000 1.688 Ib/1000 .028Ibs/1000 Test Due

AIRS No.: Period

1100003 Comments NOWCEM

Comments:

AODAQE: OPNo.: MACT SUBPART UUU

AO Date: OP Date: Location: Size: A NSPS Subpart: MACT UUU

Method Limitation LastTest Result Test Due Period Comments HCI 30 ppmdv 10/9/2005 0.16 ppmdv Source: Comments: FCC Boiler Stack (CO CEM) Precipitator Stack Gases .5% 02 required. Quarterly audit required. CEM review/not stack test. AIRS No.: Location: Davis Size: A 1100003

AODAQE: OPNo.: ANO119054-05 AO Date: OP Date: NSPS Subpart: 4/8/2005

Method 10 10 Limitation 500.0 PPM 42.0Ibs/hr LastTest Result Test Due Period 1 CEM Comments

Tuesday, August 07,200710:14:03 AM Page 1 of 4

## StackTests - Selected Companies Source: FCC CO Boiler & Catalyst Regen. AIRS No.: 1100003 Comments:

AO DAQE: OPNo.: AN0119056-05 AO Date: OP Date: Location: Davis Size: A NSPS Subpart: 

### J 7/20/2005

Method 

### 6 201 (a) 

### 7 201 (a) Source: Limitation Last Test Result 228.0 Ibs/hr 1/21/2003 154.3Ib/hr .0662 gr/dscf 850 ppmv 1/21/2003 55.1 Ib/hr 15.96 Ibs/hr 1/21/2003 6.5Ib/hr FCC Precipitator Test Due

1/21/2006 AIRS No.: Period Comments Test A.D.



### 3 1100003 Comments:

AODAQE: OPNo.: This stack test replaced by re-directing emissions to CO Boiler as per AO 1/18/94. This AO supercedes SIP as per H. Nellestein.
AO Date: OP Date: Location: Davis Size: 

### A NSPS Subpart: 

### J 8/10/1987

Method Limitation Last Test Result Test Due Period Comments 

### 5 .080 gr/dscf 2/27/1989 .0399 gr/dscf Process replaced Source: HCC Cracker Unit Fuel Gas Line(H2S Mon.) AIRS No.: 1100003 Comments:

AODAQE: OPNo.: H2S Monitor

AN0119056-05 AO Date: OP Date: Location: Davis Size: A NSPS Subpart: 7/20/2005

Method Limitation LastTest Result Test Due Period Comments 11 0.10 gr/dscf 12/8/1993 .0007 gr/dscf CEM Source: Comments:

AO DAQE: OPNo.: HCC Plume Boiler (historical Record Only Perm. shut down as of 10/15/93 AO. (DAQE-0923- 93) See History for previous AO dates. See source continued for additional tests.
AO Date: OP Date: AIRS No.: Location: Davis Size: 

### A NSPS Subpart: 3/17/1992 1100003

Method Limitation Last Test Result Test Due Period Comments 201 (a) 201 (a) 

### 6 6 .0502 gr/dscf 9.66 Ibs/hr 66.33 Ibs/hr 316 ppmv 4/13/1993 4/13/1993 0.547 gr/dscf 7.62Ibs/hr (shut down test) 

### 3 3 perm. shut down perm. shut down

Tuesday, August 07,200710:14:03 AM Page 2 of 4Source: HDS Furnaces 

## Stack Tests - Selected Companies AIRS No.: 1100003 Comments:

AO DAQE: OPNo.: AO Date: OP Date: Location: Davis Size: A NSPS Subpart: J 11/27/1991

Method 10 

### 6 

### 7 5 Limitation 15.24 ppmdv 9.0 ppmdv 40.8 ppmdv .021 gr/dscf Last Test Result Test Due Period Comments test A. D. test A. D. test A. D. test A. D. Source: Comments:

AO DAQE: OPNo.: Houdry CO Plume Boiler HISTORICAL RECORD ONLY - THIS FACILITY PERM. SHUT DOWN

AO Date: OP Date: AIRS No.: Location: Davis Size: A NSPS Subpart: 4/28/1987 1100003

Method Limitation Last Test Result Test Due Period Comments 201 (a) 201 (a) 

### 5 Source: Comments: 8.96Ib/hr .0662 gr/dscf .075 gr/dscf Lirne Bin Baghouse AO page 12 Condition 9D. 0.0123 gr/dsc 8/3/1 994 5.99 Ibs/href
AIRS No.: 1100003 Location: Davis Size: A
AO DAQE: OPNo.: DAQE-0923-93 AO Date: OP Date: NSPS Subpart: 10/15/1993

Method 201 (a) Source: Limitation 0.11 Ibs/hr SRU Tail Gas Stack LastTest Result Test Due

AIRS No.: Period

1100003 Comments Test A.D.

Comments:

AO DAQE: OPNo.: See source continued for RM21, and S02 ppmdv limitations.

AO Date: OP Date: Location: Davis Size: A NSPS Subpart: 

### J 11/27/1991

Method Limitation LastTest Result Test Due Period Comments 

### 5 7 10 

### 6 .0272 gr/dscf 50. ppmdv 1900. ppmdv 178.00Ibs/hr 10/28/1993 88.78Ibs/hr test A. D. test A. D. test A. 

### D. CEM after inital Tuesday, August 07,200710:14:03 AM Page 3 of 4Source: Sulfur Plant Incinerator 

## StackTests - Selected Companies AIRS No.: 1100003 Comments:

AO DACE: OPNo.: AO Date: OP Date: Location: Davis Size: A NSPS Subpart: 4/10/1998

Method 

### S02 S02 Limitation 177.3Ib/hr 7644 ppmv 

### LastTest Result Test Due Period Comments CEM

Tuesday, August 07,200710:14:03 AM Page 4 of 4