Name: Linda Boyer

Title: Manager - Compliance Services

Company: PPL Martins Creek LLC

Sign Date: 9/7/2010

Name: Jeff Kunstling

Title: Project Manager

Company: TRC Companies, Inc.

Sign Date: 9/7/2010

Permitted Facility Representative / Date Testing Company Representative / Date

Utility Boiler MACT ICR - Martins Creek Unit 4

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Tuesday, February 01, 2011 Page 1 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Facility Information:

Martins Creek Plant

6605 Foul Rift Road

Bangor PA 18013

Contact: Linda Boyer

Phone: 610-774-4400

Fax: 610-774-7136

Email: laboyer@pplweb.com

Testing Company:

TRC Companies, Inc.

5540 Centerview Drive

Suite 100

Raleigh NC 27606

Contact:Jeff Kunstling

Phone: 919-256-6234

Fax: 919-838-9661

Email: jkunstling@trcsolutions.com

Air Permit Number:

3148

Permitted Source ID/Name:

4

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

Unit 4 is capable of firing No. 2 oil, No. 6 oil, and natural gas and has a power output nominally rated at 870 

megawatts.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 4209500004 FRS #: 110000334656

SCC / Description 10100401 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Normal Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 298 0 0 0 3180 2940 4 3

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Tuesday, February 01, 2011 Page 2 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 3 480 0

Stack Exit Other PeCDD Method 23 3 480 0

Stack Exit Other HxCDD Method 23 3 480 0

Stack Exit Other HpCDD Method 23 3 480 0

Stack Exit Other TCDF Method 23 3 480 0

Stack Exit Other PeCDF Method 23 3 480 0

Stack Exit Other HxCDF Method 23 3 480 0

Stack Exit Other HpCDF Method 23 3 480 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Method 25A 3 120 0 NMHC emissions 

only. Methane 

emissions reported in 

excel template.

Stack Exit

Stack Exit Hydrogen Chloride Method 26A 3 60 0

Stack Exit Hydrogen Fluoride Method 26A 3 60 0

Stack Exit Filterable Particulate OTM - 27/28 3 240 0

Stack Exit Total Particulate OTM - 27/28 3 240 0

Inorganic (Aqueous) 

Condensible Part.

Stack Exit OTM - 27/28 3 240 0

Stack Exit Total PM2.5 OTM - 27/28 3 240 0

Stack Exit Filterable PM2.5 OTM - 27/28 3 240 0

Organic Condensible 

Particulate

Stack Exit OTM - 27/28 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Cobalt Method 29 3 240 0

Tuesday, February 01, 2011 Page 3 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Stack Exit Chromium Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Sulfur Dioxide Method 6C 3 60 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 60 0

Tuesday, February 01, 2011 Page 4 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Sampling / Stack Data Results Summary

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 7/20/2010 7/21/2010 7/22/2010

Run Start Time 10:01:00 AM 6:12:00 

AM

6:40:00 AM

Run Finish Time 7:02:00 PM 9:35:00 PM 4:45:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 380.771 350.702 362.803 364.759

Moisture Content of Stack Gas, % 10.53 11.08 10.20 10.603

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.4 10.5 10.8 10.567

Oxygen, % 7.5 7.5 7.1 7.367

Average Stack Gas Temperature, °F 304.33 303.65 308.33 305.437

Dry Volumetric Flow Rate, dry scfm 1,035,820.7 979,248.3 1,023,523.1 1,012,864.03

3

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,714,311.9 1,631,487.9 1,692,516.1 1,679,438.63

3

Percent Isokinetic of Sampling Rate, % 100.6 99.5 98.5 99.533

F-Factor, dscfm/MMBtu @ %O2 9472 9472 9472 9,472.000

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 5 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Tuesday, February 01, 2011 Page 6 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Tuesday, February 01, 2011 Page 7 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Tuesday, February 01, 2011 Page 8 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Emissions Summary

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

lb/mmBtuO2 -1.04E-03 -9.87E-04 -2.08E-03 -0.001

ppm -9.88E-01 -9.43E-01 -1.99E+00 -1.307

ppm@7%O2 -1.01E+00 -9.53E-01 -2.01E+00 -1.324

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000875 0.00000000937 0.0000000137 0.000

lb/mmBtuO2 7.48E-13 8.70E-13 1.19E-12 0.000

ng/dscm 8.12E-04 9.44E-04 1.33E-03 0.001

ng/dscm@7%O2 8.42E-04 9.79E-04 1.34E-03 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000627 0.00000000413 0.00000000885 0.000

lb/mmBtuO2 5.36E-13 3.84E-13 7.71E-13 0.000

ng/dscm 5.82E-04 4.16E-04 8.62E-04 0.001

ng/dscm@7%O2 6.04E-04 4.32E-04 8.68E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000399 0.00000000513 0.00000000458 0.000

lb/mmBtuO2 3.41E-13 4.76E-13 3.99E-13 0.000

ng/dscm 3.70E-04 5.17E-04 4.46E-04 0.000

ng/dscm@7%O2 3.84E-04 5.36E-04 4.49E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000171 0.00000000195 0.00000000172 0.000

lb/mmBtuO2 1.46E-13 1.81E-13 1.50E-13 0.000

ng/dscm 1.59E-04 1.96E-04 1.67E-04 0.000

ng/dscm@7%O2 1.65E-04 2.03E-04 1.68E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000446 0.00000000231 0.00000000641 0.000

lb/mmBtuO2 3.81E-13 2.15E-13 5.59E-13 0.000

ng/dscm 4.14E-04 2.33E-04 6.24E-04 0.000

ng/dscm@7%O2 4.29E-04 2.42E-04 6.29E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

Tuesday, February 01, 2011 Page 9 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

RunNumber 1 2 3

Mass_mg 0.00000000189 0.00000000196 0.00000000167 0.000

lb/mmBtuO2 1.62E-13 1.82E-13 1.46E-13 0.000

ng/dscm 1.75E-04 1.97E-04 1.63E-04 0.000

ng/dscm@7%O2 1.82E-04 2.04E-04 1.64E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000234 0.0000000019 0.00000000359 0.000

lb/mmBtuO2 2.00E-13 1.76E-13 3.13E-13 0.000

ng/dscm 2.17E-04 1.91E-04 3.49E-04 0.000

ng/dscm@7%O2 2.25E-04 1.98E-04 3.52E-04 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000186 0.00000000246 0.00000000296 0.000

lb/mmBtuO2 1.59E-13 2.28E-13 2.58E-13 0.000

ng/dscm 1.73E-04 2.48E-04 2.88E-04 0.000

ng/dscm@7%O2 1.79E-04 2.57E-04 2.90E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000134 0.00000000129 0.00000000122 0.000

lb/mmBtuO2 1.15E-13 1.20E-13 1.06E-13 0.000

ng/dscm 1.24E-04 1.30E-04 1.19E-04 0.000

ng/dscm@7%O2 1.29E-04 1.35E-04 1.20E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000183 0.00000000219 0.0000000015 0.000

lb/mmBtuO2 1.57E-13 2.03E-13 1.31E-13 0.000

ng/dscm 1.70E-04 2.21E-04 1.46E-04 0.000

ng/dscm@7%O2 1.76E-04 2.29E-04 1.47E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000456 0.00000000193 0.00000000548 0.000

lb/mmBtuO2 3.90E-13 1.79E-13 4.78E-13 0.000

ng/dscm 4.23E-04 1.94E-04 5.33E-04 0.000

ng/dscm@7%O2 4.39E-04 2.01E-04 5.37E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.00000000758 0.0000000093 0.000000027 0.000

lb/mmBtuO2 6.48E-13 8.64E-13 2.35E-12 0.000

ng/dscm 7.03E-04 9.37E-04 2.63E-03 0.001

ng/dscm@7%O2 7.29E-04 9.72E-04 2.65E-03 0.001

Tuesday, February 01, 2011 Page 10 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000106 0.0000001422 0.0000001812 0.000

lb/mmBtuO2 9.07E-12 1.32E-11 1.58E-11 0.000

ng/dscm 9.83E-03 1.43E-02 1.76E-02 0.014

ng/dscm@7%O2 1.02E-02 1.48E-02 1.77E-02 0.014

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000969 0.000000994 0.00000132 0.000

lb/mmBtuO2 8.29E-11 9.23E-11 1.15E-10 0.000

ng/dscm 8.99E-02 1.00E-01 1.29E-01 0.106

ng/dscm@7%O2 9.33E-02 1.04E-01 1.30E-01 0.109

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000525 0.0000000624 0.0000000804 0.000

lb/mmBtuO2 4.49E-12 5.80E-12 7.01E-12 0.000

ng/dscm 4.87E-03 6.28E-03 7.83E-03 0.006

ng/dscm@7%O2 5.05E-03 6.51E-03 7.89E-03 0.006

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000102 0.0000001 0.000000123 0.000

lb/mmBtuO2 8.72E-12 9.29E-12 1.07E-11 0.000

ng/dscm 9.46E-03 1.01E-02 1.20E-02 0.011

ng/dscm@7%O2 9.81E-03 1.05E-02 1.21E-02 0.011

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000321 0.00000345 0.00000397 0.000

lb/mmBtuO2 2.75E-10 3.20E-10 3.46E-10 0.000

ng/dscm 2.98E-01 3.47E-01 3.86E-01 0.344

ng/dscm@7%O2 3.09E-01 3.60E-01 3.89E-01 0.353

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000114 0.0000000917 0.000000118 0.000

lb/mmBtuO2 9.75E-12 8.52E-12 1.03E-11 0.000

ng/dscm 1.06E-02 9.24E-03 1.15E-02 0.010

ng/dscm@7%O2 1.10E-02 9.58E-03 1.16E-02 0.011

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000275 0.0000000012 0.00000000351 0.000

lb/mmBtuO2 2.35E-13 1.11E-13 3.06E-13 0.000

Tuesday, February 01, 2011 Page 11 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

ng/dscm 2.55E-04 1.21E-04 3.42E-04 0.000

ng/dscm@7%O2 2.65E-04 1.26E-04 3.44E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000157 0.0000000018 0.00000000422 0.000

lb/mmBtuO2 1.34E-13 1.67E-13 3.68E-13 0.000

ng/dscm 1.46E-04 1.81E-04 4.11E-04 0.000

ng/dscm@7%O2 1.51E-04 1.88E-04 4.14E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000148 0.00000000129 0.00000000117 0.000

lb/mmBtuO2 1.27E-13 1.20E-13 1.02E-13 0.000

ng/dscm 1.37E-04 1.30E-04 1.14E-04 0.000

ng/dscm@7%O2 1.42E-04 1.35E-04 1.15E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000843 0.00000000172 0.00000000852 0.000

lb/mmBtuO2 7.21E-13 1.60E-13 7.43E-13 0.000

ng/dscm 7.82E-04 1.73E-04 8.29E-04 0.001

ng/dscm@7%O2 8.11E-04 1.79E-04 8.35E-04 0.001

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000000703 0.0000000063 0.0000000079 0.000

lb/mmBtuO2 6.01E-13 5.85E-13 6.89E-13 0.000

ng/dscm 6.52E-04 6.34E-04 7.69E-04 0.001

ng/dscm@7%O2 6.76E-04 6.58E-04 7.75E-04 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000251 0.0000000197 0.0000000244 0.000

lb/mmBtuO2 2.15E-12 1.83E-12 2.13E-12 0.000

ng/dscm 2.33E-03 1.98E-03 2.38E-03 0.002

ng/dscm@7%O2 2.42E-03 2.05E-03 2.40E-03 0.002

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.00000069 0.000000689 0.000001 0.000

lb/mmBtuO2 5.90E-11 6.40E-11 8.72E-11 0.000

ng/dscm 6.40E-02 6.94E-02 9.74E-02 0.077

ng/dscm@7%O2 6.64E-02 7.20E-02 9.81E-02 0.079

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Tuesday, February 01, 2011 Page 12 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Mass_mg 0.000000054 0.0000000543 0.0000000718 0.000

lb/mmBtuO2 4.62E-12 5.04E-12 6.26E-12 0.000

ng/dscm 5.01E-03 5.47E-03 6.99E-03 0.006

ng/dscm@7%O2 5.20E-03 5.67E-03 7.04E-03 0.006

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000257 0.0000000395 0.0000000416 0.000

lb/mmBtuO2 2.20E-12 3.67E-12 3.63E-12 0.000

ng/dscm 2.38E-03 3.98E-03 4.05E-03 0.003

ng/dscm@7%O2 2.47E-03 4.13E-03 4.08E-03 0.004

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000522 0.00000000561 0.00000000694 0.000

lb/mmBtuO2 4.47E-13 5.21E-13 6.05E-13 0.000

ng/dscm 4.84E-04 5.65E-04 6.76E-04 0.001

ng/dscm@7%O2 5.02E-04 5.86E-04 6.81E-04 0.001

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000155 0.0000000203 0.0000000242 0.000

lb/mmBtuO2 1.33E-12 1.89E-12 2.11E-12 0.000

ng/dscm 1.44E-03 2.04E-03 2.36E-03 0.002

ng/dscm@7%O2 1.49E-03 2.12E-03 2.38E-03 0.002

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000322 0.0000000267 0.0000000396 0.000

lb/mmBtuO2 2.75E-12 2.48E-12 3.45E-12 0.000

ng/dscm 2.99E-03 2.69E-03 3.86E-03 0.003

ng/dscm@7%O2 3.10E-03 2.79E-03 3.89E-03 0.003

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000106 0.00000000174 0.000000016 0.000

lb/mmBtuO2 9.07E-13 1.62E-13 1.39E-12 0.000

ng/dscm 9.83E-04 1.75E-04 1.56E-03 0.001

ng/dscm@7%O2 1.02E-03 1.82E-04 1.57E-03 0.001

Tuesday, February 01, 2011 Page 13 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000378 0.0000000267 0.0000000392 0.000

lb/mmBtuO2 3.23E-12 2.48E-12 3.42E-12 0.000

ng/dscm 3.51E-03 2.69E-03 3.82E-03 0.003

ng/dscm@7%O2 3.64E-03 2.79E-03 3.85E-03 0.003

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000167 0.00000000997 0.0000000284 0.000

lb/mmBtuO2 1.43E-12 9.26E-13 2.48E-12 0.000

ng/dscm 1.55E-03 1.00E-03 2.76E-03 0.002

ng/dscm@7%O2 1.61E-03 1.04E-03 2.78E-03 0.002

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000052 0.0000000177 0.0000000853 0.000

lb/mmBtuO2 4.45E-12 1.64E-12 7.44E-12 0.000

ng/dscm 4.82E-03 1.78E-03 8.30E-03 0.005

ng/dscm@7%O2 5.00E-03 1.85E-03 8.36E-03 0.005

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000745 0.0000000187 0.00000016 0.000

lb/mmBtuO2 6.37E-12 1.74E-12 1.39E-11 0.000

ng/dscm 6.91E-03 1.88E-03 1.56E-02 0.008

ng/dscm@7%O2 7.17E-03 1.95E-03 1.57E-02 0.008

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.00000018072 0.00000015012 0.00000025262 0.000

lb/mmBtuO2 1.55E-11 1.39E-11 2.20E-11 0.000

ng/dscm 1.68E-02 1.51E-02 2.46E-02 0.019

ng/dscm@7%O2 1.74E-02 1.57E-02 2.48E-02 0.019

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.00000014273 0.00000005743 0.00000025772 0.000

lb/mmBtuO2 1.22E-11 5.33E-12 2.25E-11 0.000

ng/dscm 1.32E-02 5.78E-03 2.51E-02 0.015

ng/dscm@7%O2 1.37E-02 6.00E-03 2.53E-02 0.015

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

lb/mmBtuO2 0.00E+00 1.61E-04 1.12E-04 0.000

Tuesday, February 01, 2011 Page 14 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

ppm 0.00E+00 9.78E-02 6.79E-02 0.055

ppm@7%O2 0.00E+00 9.89E-02 6.86E-02 0.056

Location: Stack Exit - Method 26A

Compound: Hydrogen Chloride

Average

RunNumber 1 2 3

Mass_mg 1.316 1.37 1.327 1.338

lb/mmBtuO2 9.26E-04 9.64E-04 9.32E-04 0.001

Compound: Hydrogen Fluoride

Average

RunNumber 1 2 3

Mass_mg 0.188 0.196 0.202 0.195

lb/mmBtuO2 1.32E-04 1.38E-04 1.42E-04 0.000

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.6301 0.4049 0.5597 0.532

lb/mmBtuO2 1.09E-04 7.43E-05 9.90E-05 0.000

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.0055 0.0124 0.0134 0.010

lb/mmBtuO2 9.49E-07 2.27E-06 2.37E-06 0.000

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.00054 0.00027 0.00038 0.000

lb/mmBtuO2 9.32E-08 4.95E-08 6.72E-08 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.00088 0.0009 0.00089 0.001

lb/mmBtuO2 1.52E-07 1.65E-07 1.57E-07 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0236 0.0443 0.0321 0.033

lb/mmBtuO2 4.07E-06 8.13E-06 5.68E-06 0.000

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.1923 0.1373 0.1713 0.167

lb/mmBtuO2 3.32E-05 2.52E-05 3.03E-05 0.000

Tuesday, February 01, 2011 Page 15 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 275.8 240.7 268.2 261.567

lb/mmBtuO2 4.76E-02 4.41E-02 4.75E-02 0.046

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0889 0.0672 0.065 0.074

lb/mmBtuO2 1.53E-05 1.23E-05 1.15E-05 0.000

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.0885 0.0839 0.1064 0.093

lb/mmBtuO2 1.53E-05 1.54E-05 1.88E-05 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 3.5094 2.5916 3.1866 3.096

lb/mmBtuO2 6.05E-04 4.75E-04 5.64E-04 0.001

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.008 0.0187 0.0131 0.013

lb/mmBtuO2 1.38E-06 3.43E-06 2.32E-06 0.000

Location: Stack Exit - Method 6C

Compound: Sulfur Dioxide

Average

Run 1 2 3

lb/mmBtuO2 5.89E-01 6.15E-01 6.16E-01 0.607

ppm 2.39E+02 2.49E+02 2.50E+02 246.000

ppm@7%O2 2.49E+02 2.59E+02 2.60E+02 256.000

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

lb/mmBtuO2 3.23E-01 3.21E-01 3.20E-01 0.321

ppm 1.82E+02 1.82E+02 1.81E+02 181.667

ppm@7%O2 1.90E+02 1.89E+02 1.88E+02 189.000

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 122.7 111 84.5 106.067

lb/mmBtuO2 4.62E-02 4.27E-02 3.26E-02 0.041

Tuesday, February 01, 2011 Page 16 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Process Run Data

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 71 87.7 67.1 75.267

lb/mmBtuO2 2.67E-02 3.38E-02 2.59E-02 0.029

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 59 23 33.3 38.433

lb/mmBtuO2 2.22E-02 8.85E-03 1.28E-02 0.015

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 8.6 17.5 2.8 9.633

lb/mmBtuO2 3.23E-03 6.74E-03 1.08E-03 0.004

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 190.3 151.5 120.6 154.133

lb/mmBtuO2 7.16E-02 5.83E-02 4.65E-02 0.059

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 138.6 128.2 103.2 123.333

lb/mmBtuO2 5.21E-02 4.93E-02 3.98E-02 0.047

Tuesday, February 01, 2011 Page 17 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 4172 Million Btus/hr Collected during 

run 1 M26A

0

10 Heat Input 4119 Million Btus/hr Collected during 

run 1 M23

0

11 Heat Input 4101 Million Btus/hr Collected during 

run 2 M23

0

12 Heat Input 4083 Million Btus/hr Collected during 

run 3 M23

0

13 Heat Input 4062 Million Btus/hr Collected during 

run 1 M10 and 

M25A

0

14 Heat Input 4099 Million Btus/hr Collected during 

run 2 M10 and 

M25A

0

15 Heat Input 4074 Million Btus/hr Collected during 

run 3 M10 and 

M25A

0

2 Heat Input 4135 Million Btus/hr Collected during 

run 2 M26A

0

3 Heat Input 4154 Million Btus/hr Collected during 

run 3 M26A

0

4 Heat Input 4166 Million Btus/hr Collected during 

run 1 M7E and 6C

0

5 Heat Input 4135 Million Btus/hr Collected during 

run 2 M7E and 6C

0

6 Heat Input 4154 Million Btus/hr Collected during 

run 3 M7E and 6C

0

7 Heat Input 4107 Million Btus/hr Collected during 

run 1 M29 and 

OTM 27/28

0

8 Heat Input 4125 Million Btus/hr Collected during 

run 2 M29 and 

OTM 27/28

0

9 Heat Input 4115 Million Btus/hr Collected during 

run 3 M29 and 

OTM 27/28

0

1 Steam Output 2555.5 Klb/hr Collected during 

run 1 M26A

0

10 Steam Output 2562 Klb/hr Collected during 

run 1 M23

0

11 Steam Output 2589.7 Klb/hr Collected during 

run 2 M23

0

Tuesday, February 01, 2011 Page 18 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

12 Steam Output 2585.1 Klb/hr Collected during 

run 3 M23

0

13 Steam Output 2533.6 Klb/hr Collected during 

run 1 M10 and 

M25A

0

14 Steam Output 2580.2 Klb/hr Collected during 

run 2 M10 and 

M25A

0

15 Steam Output 2586.1 Klb/hr Collected during 

run 3 M10 and 

M25A

0

2 Steam Output 2560.2 Klb/hr Collected during 

run 2 M26A

0

3 Steam Output 2559.5 Klb/hr Collected during 

run 3 M26A

0

4 Steam Output 2557.8 Klb/hr Collected during 

run 1 M7E and 6C

0

5 Steam Output 2560.2 Klb/hr Collected during 

run 2 M7E and 6C

0

6 Steam Output 2559.5 Klb/hr Collected during 

run 3 M7E and 6C

0

7 Steam Output 2564 Klb/hr Collected during 

run 1 M29 and 

OTM 27/28

0

8 Steam Output 2559.4 Klb/hr Collected during 

run 2 M29 and 

OTM 27/28

0

9 Steam Output 2541.4 Klb/hr Collected during 

run 3 M29 and 

OTM 27/28

0

1 No. 6 Oil Input 7.87 gal/min Collected during 

run 1 M26A

0

10 No. 6 Oil Input 7.84 gal/min Collected during 

run 1 M23

0

11 No. 6 Oil Input 7.85 gal/min Collected during 

run 2 M23

0

12 No. 6 Oil Input 7.84 gal/min Collected during 

run 3 M23

0

13 No. 6 Oil Input 7.78 gal/min Collected during 

run 1 M10 and 

M25A

0

14 No. 6 Oil Input 7.83 gal/min Collected during 

run 2 M10 and 

M25A

0

15 No. 6 Oil Input 7.84 gal/min Collected during 

run 3 M10 and 

M25A

0

Tuesday, February 01, 2011 Page 19 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

2 No. 6 Oil Input 7.85 gal/min Collected during 

run 2 M26A

0

3 No. 6 Oil Input 7.83 gal/min Collected during 

run 3 M26A

0

4 No. 6 Oil Input 7.87 gal/min Collected during 

run 1 M7E and 6C

0

5 No. 6 Oil Input 7.85 gal/min Collected during 

run 2 M7E and 6C

0

6 No. 6 Oil Input 7.83 gal/min Collected during 

run 3 M7E and 6C

0

7 No. 6 Oil Input 7.84 gal/min Collected during 

run 1 M29 and 

OTM 27/28

0

8 No. 6 Oil Input 7.85 gal/min Collected during 

run 2 M29 and 

OTM 27/28

0

9 No. 6 Oil Input 7.83 gal/min Collected during 

run 3 M29 and 

OTM 27/28

0

1 Gross Generation 368.2 MW Collected during 

run 1 M26A

0

10 Gross Generation 370 MW Collected during 

run 1 M23

0

11 Gross Generation 372.8 MW Collected during 

run 2 M23

0

12 Gross Generation 372.4 MW Collected during 

run 3 M23

0

13 Gross Generation 368.8 MW Collected during 

run 1 M10 and 

M25A

0

14 Gross Generation 372.8 MW Collected during 

run 2 M10 and 

M25A

0

15 Gross Generation 371.3 MW Collected during 

run 3 M10 and 

M25A

0

2 Gross Generation 369.9 MW Collected during 

run 2 M26A

0

3 Gross Generation 370.1 MW Collected during 

run 3 M26A

0

4 Gross Generation 368.4 MW Collected during 

run 1 M7E and 6C

0

5 Gross Generation 369.9 MW Collected during 

run 2 M7E and 6C

0

6 Gross Generation 370.1 MW Collected during 

run 3 M7E and 6C

0

Tuesday, February 01, 2011 Page 20 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

7 Gross Generation 371.5 MW Collected during 

run 1 M29 and 

OTM 27/28

0

8 Gross Generation 373.2 MW Collected during 

run 2 M29 and 

OTM 27/28

0

9 Gross Generation 373.1 MW Collected during 

run 3 M29 and 

OTM 27/28

0

1 Net Generation 346.4 MW Collected during 

run 1 M26A

0

10 Net Generation 348 MW Collected during 

run 1 M23

0

11 Net Generation 351.1 MW Collected during 

run 2 M23

0

12 Net Generation 350.5 MW Collected during 

run 3 M23

0

13 Net Generation 347.2 MW Collected during 

run 1 M10 and 

M25A

0

14 Net Generation 351 MW Collected during 

run 2 M10 and 

M25A

0

15 Net Generation 349.4 MW Collected during 

run 3 M10 and 

M25A

0

2 Net Generation 348.1 MW Collected during 

run 2 M26A

0

3 Net Generation 348.2 MW Collected during 

run 3 M26A

0

4 Net Generation 346.4 MW Collected during 

run 1 M7E and 6C

0

5 Net Generation 348.1 MW Collected during 

run 2 M7E and 6C

0

6 Net Generation 348.2 MW Collected during 

run 3 M7E and 6C

0

7 Net Generation 349.6 MW Collected during 

run 1 M29 and 

OTM 27/28

0

8 Net Generation 351.3 MW Collected during 

run 2 M29 and 

OTM 27/28

0

9 Net Generation 351.2 MW Collected during 

run 3 M29 and 

OTM 27/28

0

1 Economizer Outlet O2 5.6 % Collected during 

run 1 M26A

0

Tuesday, February 01, 2011 Page 21 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

10 Economizer Outlet O2 5.5 % Collected during 

run 1 M23

0

11 Economizer Outlet O2 5 % Collected during 

run 2 M23

0

12 Economizer Outlet O2 5.1 % Collected during 

run 3 M23

0

13 Economizer Outlet O2 5.2 % Collected during 

run 1 M10 and 

M25A

0

14 Economizer Outlet O2 5.1 % Collected during 

run 2 M10 and 

M25A

0

15 Economizer Outlet O2 5.2 % Collected during 

run 3 M10 and 

M25A

0

2 Economizer Outlet O2 5.6 % Collected during 

run 2 M26A

0

3 Economizer Outlet O2 5.6 % Collected during 

run 3 M26A

0

4 Economizer Outlet O2 5.6 % Collected during 

run 1 M7E and 6C

0

5 Economizer Outlet O2 5.6 % Collected during 

run 2 M7E and 6C

0

6 Economizer Outlet O2 5.6 % Collected during 

run 3 M7E and 6C

0

7 Economizer Outlet O2 5.5 % Collected during 

run 1 M29 and 

OTM 27/28

0

8 Economizer Outlet O2 5.6 % Collected during 

run 2 M29 and 

OTM 27/28

0

9 Economizer Outlet O2 5.5 % Collected during 

run 3 M29 and 

OTM 27/28

0

1 No. 2 Oil Flow 0 gal/hr Collected during 

run 1 M26A

0

10 No. 2 Oil Flow 0 gal/hr Collected during 

run 1 M23

0

11 No. 2 Oil Flow 0 gal/hr Collected during 

run 2 M23

0

12 No. 2 Oil Flow 0 gal/hr Collected during 

run 3 M23

0

13 No. 2 Oil Flow 0 gal/hr Collected during 

run 1 M10 and 

M25A

0

Tuesday, February 01, 2011 Page 22 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

14 No. 2 Oil Flow 0 gal/hr Collected during 

run 2 M10 and 

M25A

0

15 No. 2 Oil Flow 0 gal/hr Collected during 

run 3 M10 and 

M25A

0

2 No. 2 Oil Flow 0 gal/hr Collected during 

run 2 M26A

0

3 No. 2 Oil Flow 0 gal/hr Collected during 

run 3 M26A

0

4 No. 2 Oil Flow 0 gal/hr Collected during 

run 1 M7E and 6C

0

5 No. 2 Oil Flow 0 gal/hr Collected during 

run 2 M7E and 6C

0

6 No. 2 Oil Flow 0 gal/hr Collected during 

run 3 M7E and 6C

0

7 No. 2 Oil Flow 0 gal/hr Collected during 

run 1 M29 and 

OTM 27/28

0

8 No. 2 Oil Flow 0 gal/hr Collected during 

run 2 M29 and 

OTM 27/28

0

9 No. 2 Oil Flow 0 gal/hr Collected during 

run 3 M29 and 

OTM 27/28

0

1 Natural Gas Flow 301 scfh Collected during 

run 1 M26A

0

10 Natural Gas Flow 300 scfh Collected during 

run 1 M23

0

11 Natural Gas Flow 308 scfh Collected during 

run 2 M23

0

12 Natural Gas Flow 303 scfh Collected during 

run 3 M23

0

13 Natural Gas Flow 299 scfh Collected during 

run 1 M10 and 

M25A

0

14 Natural Gas Flow 305 scfh Collected during 

run 2 M10 and 

M25A

0

15 Natural Gas Flow 300 scfh Collected during 

run 3 M10 and 

M25A

0

2 Natural Gas Flow 302 scfh Collected during 

run 2 M26A

0

3 Natural Gas Flow 302 scfh Collected during 

run 3 M26A

0

Tuesday, February 01, 2011 Page 23 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

4 Natural Gas Flow 301 scfh Collected during 

run 1 M7E and 6C

0

5 Natural Gas Flow 302 scfh Collected during 

run 2 M7E and 6C

0

6 Natural Gas Flow 302 scfh Collected during 

run 3 M7E and 6C

0

7 Natural Gas Flow 303 scfh Collected during 

run 1 M29 and 

OTM 27/28

0

8 Natural Gas Flow 304 scfh Collected during 

run 2 M29 and 

OTM 27/28

0

9 Natural Gas Flow 304 scfh Collected during 

run 3 M29 and 

OTM 27/28

0

1 Average Stack Exit CO2 9.3 % Collected during 

run 1 M26A

0

10 Average Stack Exit CO2 9.3 % Collected during 

run 1 M23

0

11 Average Stack Exit CO2 9.4 % Collected during 

run 2 M23

0

12 Average Stack Exit CO2 9.4 % Collected during 

run 3 M23

0

13 Average Stack Exit CO2 9.3 % Collected during 

run 1 M10 and 

M25A

0

14 Average Stack Exit CO2 9.4 % Collected during 

run 2 M10 and 

M25A

0

15 Average Stack Exit CO2 9.4 % Collected during 

run 3 M10 and 

M25A

0

2 Average Stack Exit CO2 9.3 % Collected during 

run 2 M26A

0

3 Average Stack Exit CO2 9.3 % Collected during 

run 3 M26A

0

4 Average Stack Exit CO2 9.3 % Collected during 

run 1 M7E and 6C

0

5 Average Stack Exit CO2 9.3 % Collected during 

run 2 M7E and 6C

0

6 Average Stack Exit CO2 9.3 % Collected during 

run 3 M7E and 6C

0

7 Average Stack Exit CO2 9.3 % Collected during 

run 1 M29 and 

OTM 27/28

0

Tuesday, February 01, 2011 Page 24 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

8 Average Stack Exit CO2 9.1 % Collected during 

run 2 M29 and 

OTM 27/28

0

9 Average Stack Exit CO2 9.1 % Collected during 

run 3 M29 and 

OTM 27/28

0

1 Average Flue Gas Flow 1117 kwscfm Collected during 

run 1 M26A

0

10 Average Flue Gas Flow 1100 kwscfm Collected during 

run 1 M23

0

11 Average Flue Gas Flow 1086 kwscfm Collected during 

run 2 M23

0

12 Average Flue Gas Flow 1079 kwscfm Collected during 

run 3 M23

0

13 Average Flue Gas Flow 1087 kwscfm Collected during 

run 1 M10 and 

M25A

0

14 Average Flue Gas Flow 1086 kwscfm Collected during 

run 2 M10 and 

M25A

0

15 Average Flue Gas Flow 1078 kwscfm Collected during 

run 3 M10 and 

M25A

0

2 Average Flue Gas Flow 1105 kwscfm Collected during 

run 2 M26A

0

3 Average Flue Gas Flow 1109 kwscfm Collected during 

run 3 M26A

0

4 Average Flue Gas Flow 1116 kwscfm Collected during 

run 1 M7E and 6C

0

5 Average Flue Gas Flow 1105 kwscfm Collected during 

run 2 M7E and 6C

0

6 Average Flue Gas Flow 1109 kwscfm Collected during 

run 3 M7E and 6C

0

7 Average Flue Gas Flow 1097 kwscfm Collected during 

run 1 M29 and 

OTM 27/28

0

8 Average Flue Gas Flow 1123 kwscfm Collected during 

run 2 M29 and 

OTM 27/28

0

9 Average Flue Gas Flow 1122 kwscfm Collected during 

run 3 M29 and 

OTM 27/28

0

1 Average Stack Exit Temperature 303.2 degrees F Collected during 

run 1 M26A

0

10 Average Stack Exit Temperature 305.2 degrees F Collected during 

run 1 M23

0

Tuesday, February 01, 2011 Page 25 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

11 Average Stack Exit Temperature 300.2 degrees F Collected during 

run 2 M23

0

12 Average Stack Exit Temperature 304.7 degrees F Collected during 

run 3 M23

0

13 Average Stack Exit Temperature 305 degrees F Collected during 

run 1 M10 and 

M25A

0

14 Average Stack Exit Temperature 303.1 degrees F Collected during 

run 2 M10 and 

M25A

0

15 Average Stack Exit Temperature 305.2 degrees F Collected during 

run 3 M10 and 

M25A

0

2 Average Stack Exit Temperature 304.5 degrees F Collected during 

run 2 M26A

0

3 Average Stack Exit Temperature 305.1 degrees F Collected during 

run 3 M26A

0

4 Average Stack Exit Temperature 303.6 degrees F Collected during 

run 1 M7E and 6C

0

5 Average Stack Exit Temperature 304.5 degrees F Collected during 

run 2 M7E and 6C

0

6 Average Stack Exit Temperature 305.1 degrees F Collected during 

run 3 M7E and 6C

0

7 Average Stack Exit Temperature 304.8 degrees F Collected during 

run 1 M29 and 

OTM 27/28

0

8 Average Stack Exit Temperature 303.4 degrees F Collected during 

run 2 M29 and 

OTM 27/28

0

9 Average Stack Exit Temperature 303 degrees F Collected during 

run 3 M29 and 

OTM 27/28

0

1 Average Stack Exit Pressure 0.987 atm Collected during 

run 1 M26A

0

10 Average Stack Exit Pressure 0.988 atm Collected during 

run 1 M23

0

11 Average Stack Exit Pressure 0.986 atm Collected during 

run 2 M23

0

12 Average Stack Exit Pressure 0.988 atm Collected during 

run 3 M23

0

13 Average Stack Exit Pressure 0.988 atm Collected during 

run 1 M10 and 

M25A

0

14 Average Stack Exit Pressure 0.989 atm Collected during 

run 2 M10 and 

M25A

0

Tuesday, February 01, 2011 Page 26 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

15 Average Stack Exit Pressure 0.988 atm Collected during 

run 3 M10 and 

M25A

0

2 Average Stack Exit Pressure 0.989 atm Collected during 

run 2 M26A

0

3 Average Stack Exit Pressure 0.989 atm Collected during 

run 3 M26A

0

4 Average Stack Exit Pressure 0.988 atm Collected during 

run 1 M7E and 6C

0

5 Average Stack Exit Pressure 0.989 atm Collected during 

run 2 M7E and 6C

0

6 Average Stack Exit Pressure 0.989 atm Collected during 

run 3 M7E and 6C

0

7 Average Stack Exit Pressure 0.988 atm Collected during 

run 1 M29 and 

OTM 27/28

0

8 Average Stack Exit Pressure 0.988 atm Collected during 

run 2 M29 and 

OTM 27/28

0

9 Average Stack Exit Pressure 0.987 atm Collected during 

run 3 M29 and 

OTM 27/28

0

1 Average Ambient Pressure 0.981 atm Collected during 

run 1 M26A

0

10 Average Ambient Pressure 0.982 atm Collected during 

run 1 M23

0

11 Average Ambient Pressure 0.98 atm Collected during 

run 2 M23

0

12 Average Ambient Pressure 0.982 atm Collected during 

run 3 M23

0

13 Average Ambient Pressure 0.981 atm Collected during 

run 1 M10 and 

M25A

0

14 Average Ambient Pressure 0.982 atm Collected during 

run 2 M10 and 

M25A

0

15 Average Ambient Pressure 0.982 atm Collected during 

run 3 M10 and 

M25A

0

2 Average Ambient Pressure 0.982 atm Collected during 

run 2 M26A

0

3 Average Ambient Pressure 0.982 atm Collected during 

run 3 M26A

0

4 Average Ambient Pressure 0.981 atm Collected during 

run 1 M7E and 6C

0

5 Average Ambient Pressure 0.982 atm Collected during 

run 2 M7E and 6C

0

Tuesday, February 01, 2011 Page 27 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

APCD Run Data

Process Lab Run Data

6 Average Ambient Pressure 0.982 atm Collected during 

run 3 M7E and 6C

0

7 Average Ambient Pressure 0.981 atm Collected during 

run 1 M29 and 

OTM 27/28

0

8 Average Ambient Pressure 0.982 atm Collected during 

run 2 M29 and 

OTM 27/28

0

9 Average Ambient Pressure 0.981 atm Collected during 

run 3 M29 and 

OTM 27/28

0

Tuesday, February 01, 2011 Page 28 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Sampling / Stack Data Results Detail

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Tuesday, February 01, 2011 Page 29 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 7/20/2010 7/21/2010 7/22/2010

Run Start Time 10:01:00 AM 6:12:00 AM 6:40:00 AM

Run Finish Time 7:02:00 PM 9:35:00 PM 4:45:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.26 0.258 0.258 0.259

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9938 0.9938 0.9938 0.994

Barometric Pressure, inches of Mercury 29.32 29.29 29.32 29.310

Average Orifice Meter Differential, inches H2O 2.14 1.88 2.02 2.013

Dry Gas Meter Volume Sampled, cubic feet 402.128 366.873 380.256 383.086

Average Dry Gas Meter Temperature, °F 85.96 79.90 81.67 82.510

Dry Gas Meter Volume Sampled, dscf 380.771 350.702 362.803 364.759

Total Moisture Liquid collected, g 951.9 928.5 875.3 918.567

Volume of Water Vapor, standard cubic feet 44.81 43.70 41.20 43.237

Moisture Content of Stack Gas, % 10.53 11.08 10.20 10.603

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8947 0.8892 0.898 0.894

Carbon Dioxide, % 10.4 10.5 10.8 10.567

Oxygen, % 7.5 7.5 7.1 7.367

Carbon Monoxide & Nitrogen, % 82.1 82 82.1 82.067

Fuel Factor 1.29 1.28 1.28

Dry Molecular Weight, lb/lb-Mole 29.96 29.98 30.01 29.983

Wet Molecular weight, lb/lb-Mole 28.70 28.65 28.78 28.710

Flue Gas Static Pressure, inches of H2O -0.92 -1.1 0 -0.673

Absolute Flue Gas Pressure, inches of Mercury 29.25 29.21 29.32 29.260

Average Stack Gas Temperature, °F 304.33 303.65 308.33 305.437

Average Velocity Head, inches of H2O 0.7411459316

08073

0.669696514

747842

0.722410948

338671

0.711

Average Stack Gas Velocity, feet/second 58.99 56.14 58.24 57.790

Stack Cross-Sectional Area, square feet 484.351 484.351 484.351 484.351

Dry Volumetric Flow Rate, dry scfm 1,035,820.7 979,248.3 1,023,523.1 1,012,864.0

33

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,714,311.9 1,631,487.9 1,692,516.1 1,679,438.6

33

Percent Isokinetic of Sampling Rate, % 100.6 99.5 98.5 99.533

Percent Excess Air, % 52.9 53.0 48.7 51.533

F-Factor, dscfm/MMBtu @ %O2 9472 9472 9472 9,472.000

Round Duct Diameter, inches 298 298 298

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 0 0 0 0.000

Fc 0 0 0 0.000

Tuesday, February 01, 2011 Page 30 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Tuesday, February 01, 2011 Page 31 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 26A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Tuesday, February 01, 2011 Page 32 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Tuesday, February 01, 2011 Page 33 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Tuesday, February 01, 2011 Page 34 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Tuesday, February 01, 2011 Page 35 of 36
Utility Boiler MACT ICR - Martins Creek Unit 4

9/7/2010

Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Tuesday, February 01, 2011 Page 36 of 36