EMISSIONS TEST REPORT 

POLK POWER STATION 

FACILITY ID NUMBER: 1050233 

EMISSION UNIT ID NO: -001 

UNIT 1 

SYNTHETIC GAS 

CARBON MONOXIDE, OXIDES OF NITROGEN, 

SULFUR DIOXIDE 

and 

VISIBLE EMISSIONS EVALUATION 

January 18, 2006 

Prepared For: 

Tampa Electric Company 

Polk Power Station 

P.O. Box 111 

Tampa, Florida 33601-0111 

Prepared By: 

Tampa Electric Company 

Environmental, Health and Safety 

Environmental Services, Air Services Group 

Environmental Services 

Air Services Group 

5010 Causeway Boulevard

Tampa, Florida 33619- 6130 
REPORT CERTIFICATION 

I have reviewed the test performance, associated quality assurance 

activities, the resultant calculations, and the contents of this report, and certify 

that all project quality objectives have been met. This report is approved for 

submittal. 

Signature:__________________________ 

Raymond A. McDarby, Jr. 

Senior Environmental Technician 

Quality Assurance/Quality Control Specialist

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

The sampling and subsequent data entry/reduction detailed in this report

were conducted at my direction, and I hereby certify that this test report is 

authentic and accurate to the best of my knowledge. 

Signature:__________________________ 

Juan F. Ramirez 

Environmental Technician 

Test Team Lead 

Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 

I have reviewed the testing details and results submitted in this report, 

and hereby certify that this test report is authentic and accurate to the best of 

my knowledge. 

Signature:__________________________ 

David A. Smith 

Coordinator – Air Services Group 

Environmental Health & Safety 

Tampa Electric Company 
TABLE OF CONTENTS

SECTION PAGE NO.

1.0 INTRODUCTION 1 

2.0 DISCUSSION OF RESULTS 2 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES 3 

4.0 TABULATED RESULTS 

CARBON MONOXIDE TEST DATA 5 

NITROGEN OXIDES & SULFUR DIOXIDE DATA FROM CEMS 6 

HEAT INPUT CALCULATIONS 7 

5.0 STACK SAMPLING LOCATION DIAGRAM 9 

APPENDICES

A. CARBON MONOXIDE TEST INFORMATION

SUMMARIZED RUN DATA & QA/QC 

TEST RUN LOG 

CYLINDER GAS CERTIFICATES 

B. TURBINE DATA

C. FUEL ANALYSIS

D. CEMS DATA

E. VISIBLE EMISSION DATA SHEET

F. TEST PARTICIPANTS
1 

1.0 INTRODUCTION

On January 18, 2006, Tampa Electric Company’s, Environmental Services, Air Services 

Group performed Carbon Monoxide (CO) source emission tests, and Visible Emissions 

Observations on Unit No. 1 at the Polk Power Station. Unit No. 1 is a combined cycle 

combustion turbine generating unit. The combustion turbine was fired with syngas from 

the solid fuel gasification system. A blend of petroleum coke and bituminous coal was 

gasified for this test. Testing was conducted according to United States Environmental 

Protection Agency (USEPA) test methods stipulated in 40 CFR Part 60, Appendix A and 

Florida Department of Environmental Protection (FDEP) Permit No. 1050233-016-AV. 

Nitrogen Oxides (NOx) and Sulfur Dioxide (SO2) data was taken from the Continuous 

Emissions Monitoring System’s (CEMS) Data Acquisition and Handling System (DAHS) 

and is presented as averages over the test period. 
2 

2.0 DISCUSSION OF RESULTS

The Carbon Monoxide (CO) concentration and emission rate was derived from three 1-

hour test runs. The calculated average CO concentration was 3 ppmvd @ 15% O2. 

The calculated average emission rate was 9 lbs/hr. The FDEP permitted concentration 

is 25 ppmvd @15% O2. The FDEP permitted emission rate is 98 lbs/hr based on a 30-

day rolling average. 

The Visible Emissions Observations (VEO) yielded an average opacity of 0% for the 1-

hour test. The FDEP permitted opacity is 10 percent. 

During the CO testing, the Nitrogen Oxides (NOx) concentration averaged 11 ppmvd @ 

15% O2, with an average emission rate of 84 lbs/hr. 

During the CO testing, the Sulfur Dioxide (SO2) concentration averaged 0.11 lb/mmBtu, 

with an average emission rate of 178 lbs/hr. 

During the test Unit No. 1 was operated at an average heat input of 1649 mmBtu/hr. 

The FDEP permitted heat input is 1755 mmBtu/hr, at an ambient temperature of 59o 

(corrected to 1754 mmBtu/hr based on an average inlet vane temperature of 61oF, and 

the manufacturer’s heat input correction curve for this unit). The calculated capacity 

factor during the test was 94%. 
3 

3.0 SOURCE DESCRIPTION/TEST PROCEDURES

Polk Power Electrical Generating Station is located at County Road 630 approximately 

13 miles southwest of Bartow, Polk County, Florida. Unit No. 1 is a Combined Cycle 

Combustion Turbine generating unit, with a net capacity of 192 MW when fired with 

Syngas fuel. The source sampling location consists of a circular stack 19 feet in 

diameter with four sample ports located 90 degrees apart on the stack circumference. 

A diagram of the stack sampling location is included along with other pertinent 

information on the test site. 

Carbon Monoxide sampling was performed in accordance with USEPA Reference 

Method 10 (40 CFR Part 60, Appendix A) “Determination of Carbon Monoxide 

Emissions From Stationary Sources”. Testing was performed using a Thermo 

Environmental Instruments model 48C Carbon Monoxide Analyzer. 

Sulfur Dioxide and Nitrogen Oxides emissions data were taken from the CEMS DAHS. 

This data was taken as 1-minute averages over the time frame from 01/18/2006 12:12 

through 01/18/2006 15:42, representing the time frame of the CO test. 

Plant operational data was taken from the Plant Information (PI) server system. Data 

captured included the minute average load, minute fuel flow, minute inlet vane 

temperature, and minute saturator readings 01/18/2006 12:12 through 01/18/2006 

15:42. 
4 

4.0 TABULATED RESULTS
POLK POWER STATION

CARBON MONOXIDE DATA

CO % O2 CO, ppmvd CO

Run # Start Stop ppmvd volume @ 15% O2 lbs/hr

1 12:12 13:12 3.96 12.25 3 10

2 13:23 14:23 3.75 12.29 3 9

3 14:42 15:42 3.64 12.32 3 9

Averages: 3 9

CO, ppmvd @ 15% O2 is calculated as:

CO, ppmvd x (5.9 / (20.9 - % O2, volume))

CO, lbs/hr is calculated as:

CO, ppmvd x Cf x Fd x (20.9 / (20.9 - % O2, volume) x Heat Input

where: Cf = 7.27249E-08 lb/scf

Fd = 8378 dscf/mmBtu

Heat Input = 1649 mmBtu/hr

Test Times are Eastern Standard.

Test Times

RM Data Calculated Data

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

January 18, 2006

5 
POLK POWER STATION

NO X & SO 2 COMPLIANCE DATA FROM CEMS

NOx SO2 O2 CO2 NOx

1 NOx2 SO23 SO24

ppmvw ppmvw % w % w ppmvd @ 15% O2 lbs/hr lb/mmBtu lbs/hr

From CEMS Report: 15.22 23.18 11.04 8.22 11 84 0.11 178

1 NOx, ppmvd @ 15% O2 is calculated as:

NOx, ppmvw / (1 - % moisture) x (5.9 / (20.9 - (% O2w/ (1 - % moisture)))

where: % moisture = 0.07 assumed by CEMS

2

 NOx, lbs/hr is calculated as:

NOx, ppmvw x 1.194E-07 x Fc x (100 / % CO2w) x Heat Input, mmBtu/hr

where: Fc = 2310 scf/mmBtu, assigned F-factor for synthetic gas

Heat Input = 1649 mmBtu/hr

3

 SO2, lb/mmBtu is calculated as:

SO2, ppmvw x 1.660E-07 x Fc x (100 / % CO2w)

where: Fc = 2310 scf/mmBtu, assigned F-factor for synthetic gas

4

 SO2, lbs/hr is calculated as:

SO2, lb/mmbtu x Heat Input, mmBtu/hr

where: Heat Input = 1649 mmBtu/hr

CEM Data Calculated Data

CEMS Data are average of readings from 01/18/2006 12:13 through 15:42.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

January 18, 2006

6 
POLK POWER STATION

HEAT INPUT CALCULATION

Average fuel flow: 6878.1985 Kcfh

Mole weight correction to meter cal: 0.9883 mole weight correction factor

Corrected fuel flow:1 6797.7236 Kcfh, corrected for density

Average moisture: 5.1914037 % H20 added to fuel

Corrected fuel flow:2 6444.8263 Kscfh, corrected for moisture

Gross heating value of fuel (HHV): 255.83 Btu/scf

Heat Input: 1649 mmBtu/hr

Average fuel flow from Plant Information Data Base.

Mole weight correction factor to meter calibration is taken from ratio of syngas mole weight

to calibration gas mole weight.

1Average fuel flow times mole weight correction factor.

2Corrected fuel flow times (1 - (Average moisture / 100)).

Gross Heating value of fuel (HHV) is from fuel analysis.

Heat input is (HHV x Corrected fuel flow) / 1000.

COMBINED CYCLE COMBUSTION TURBINE

UNIT 1

January 18, 2006

7 
8 

5.0 SAMPLING LOCATION DIAGRAM
9 

UNFIRED HEAT

RECOVERY

BOILER

TRANSITION

DUCT

EXHAUST FROM

TURBINE

14 FT.

38 FT.

150 FT.

136 FT.

 PORT LOCATION PLAN

19.0 FT.ID.

STACK DIAMETERS DOWNSTREAM

FROM DISTURBANCE = 2.0

STACK DIAMETERS UPSTREAM

FROM DISTURBANCE = 0.7

STACK DIAMETER = 19.0 FT.

STACK AREA = 283.529 SQ. FT.

STACK AREA =40828.138 SQ. IN.

 TRAVERSE

 POINTS

 1 - 4.79 ”

 2 - 15.28 ”

 3 - 26.90 ”

 4 - 40.36 ”

 5 - 57.00 ”

 6 - 80.17 ”

 

 ADD 13” PORT LENGTH

 TO POINTS

Polk Power Station

Unit No. 1

IGCC

Test Location
APPENDIX A 

CARBON MONOXIDE TEST INFORMATION 
SUMMARIZED RUN DATA & QA/QC 
LabView QA Report

Polk Unit 1 Compliance - Report

RUN 1

1/18/2006 12:12:44 13:12:44

Linearity Check - Calibration Error O2 CO2 CO

Analyzer Range 25 20 10

Units % % PPM

Low Level Certified Value (PPM or %) 3.03

Mid Level Certified Value (PPM or %) 12.52 11.06 6.05

High Level Certified Value (PPM or % 20.9 18

Zero Level Observed 0.014 -0.003 -0.015

Low Level Observed - - 3.13

Mid Level Observed 12.588 11.034 6.074

High Level Observed 21.012 17.92 - 

% Difference from Zero to Target 0.06 -0.02 -0.15

% Difference from Low to Target 0 0 1

% Difference from Mid to Target 0.27 -0.13 0.24

% Difference from High to Target 0.45 -0.4 0

Analyzer Range 25 20 10

Units % % PPM

Actual Zero From Linearity 0.014 -0.003 -0.015

Actual Span From Linearity 12.588 11.034 6.074

Initial Readings

Zero 0.014 -0.003 0.039

Span 12.588 11.034 6.221

Final Readings

Zero 0.014 0.046 0.288

Span 12.527 11.034 6.396

Initial Sampling System Bias

Zero Bias (Run-System Cal) 0 0 0.54

Span Bias 0 0 1.47

Final Sampling System Bias

Zero Bias (Run-System Cal) 0 0.24 3.03

Span Bias -0.24 0 3.22

Calculated Drift

Zero Drift (Run-Run) 0 0.24 2.49

Span Drift -0.24 0 1.75

Run Results

Raw Results 12.29 8.48 4.19

Corrected Results (ppmv) 12.25 8.49 3.96

Page 1 of 3
LabView QA Report

Polk Unit 1 Compliance - Report

RUN 2

1/18/2006 13:23:19 14:23:19

Linearity Check - Calibration Error O2 CO2 CO

Analyzer Range 25 20 10

Units % % PPM

Low Level Certified Value (PPM or %) 3.03

Mid Level Certified Value (PPM or %) 12.52 11.06 6.05

High Level Certified Value (PPM or % 20.9 18

Zero Level Observed 0.014 -0.003 -0.015

Low Level Observed - - 3.13

Mid Level Observed 12.588 11.034 6.074

High Level Observed 21.012 17.92 - 

% Difference from Zero to Target 0.06 -0.02 -0.15

% Difference from Low to Target 0 0 1

% Difference from Mid to Target 0.27 -0.13 0.24

% Difference from High to Target 0.45 -0.4 0

Analyzer Range 25 20 10

Units % % PPM

Actual Zero From Linearity 0.014 -0.003 -0.015

Actual Span From Linearity 12.588 11.034 6.074

Initial Readings

Zero 0.014 0.046 0.288

Span 12.527 11.034 6.396

Final Readings

Zero -0.047 -0.003 0.293

Span 12.527 10.985 6.382

Initial Sampling System Bias

Zero Bias (Run-System Cal) 0 0.24 3.03

Span Bias -0.24 0 3.22

Final Sampling System Bias

Zero Bias (Run-System Cal) -0.24 0 3.08

Span Bias -0.24 -0.25 3.08

Calculated Drift

Zero Drift (Run-Run) -0.24 -0.24 0.05

Span Drift 0 -0.25 -0.14

Run Results

Raw Results 12.3 8.46 4.07

Corrected Results (ppmv) 12.29 8.49 3.75

Page 2 of 3
LabView QA Report

Polk Unit 1 Compliance - Report

RUN 3

1/18/2006 14:42:06 15:42:07

Linearity Check - Calibration Error O2 CO2 CO

Analyzer Range 25 20 10

Units % % PPM

Low Level Certified Value (PPM or %) 3.03

Mid Level Certified Value (PPM or %) 12.52 11.06 6.05

High Level Certified Value (PPM or % 20.9 18

Zero Level Observed 0.014 -0.003 -0.015

Low Level Observed - - 3.13

Mid Level Observed 12.588 11.034 6.074

High Level Observed 21.012 17.92 - 

% Difference from Zero to Target 0.06 -0.02 -0.15

% Difference from Low to Target 0 0 1

% Difference from Mid to Target 0.27 -0.13 0.24

% Difference from High to Target 0.45 -0.4 0

Analyzer Range 25 20 10

Units % % PPM

Actual Zero From Linearity 0.014 -0.003 -0.015

Actual Span From Linearity 12.588 11.034 6.074

Initial Readings

Zero -0.047 -0.003 0.293

Span 12.527 10.985 6.382

Final Readings

Zero 0.014 0.046 0.288

Span 12.527 10.985 6.436

Initial Sampling System Bias

Zero Bias (Run-System Cal) -0.24 0 3.08

Span Bias -0.24 -0.25 3.08

Final Sampling System Bias

Zero Bias (Run-System Cal) 0 0.24 3.03

Span Bias -0.24 -0.25 3.62

Calculated Drift

Zero Drift (Run-Run) 0.24 0.24 -0.05

Span Drift 0 0 0.54

Run Results

Raw Results 12.33 8.42 3.97

Corrected Results (ppmv) 12.32 8.47 3.64

Page 3 of 3
TEST RUN LOG 
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 7:32:00 AM 12.53 8.35 3.39

1/18/2006 7:32:30 AM 12.53 8.4 3.46

1/18/2006 7:33:00 AM 12.53 8.45 3.44

1/18/2006 7:33:30 AM 12.53 8.45 3.18

1/18/2006 7:34:00 AM 18.39 10.84 0.92

1/18/2006 7:34:30 AM 20.95 15.82 0.03

1/18/2006 7:35:00 AM Linearity Check 21.2 17.24 -0.02

1/18/2006 7:35:30 AM Linearity Check 21.01 17.92 -0.01

1/18/2006 7:36:00 AM Linearity Check 21.01 17.92 -0.01

1/18/2006 7:36:30 AM Linearity Check 7.28 7.42 3.73

1/18/2006 7:37:00 AM Linearity Check 0.14 0.34 5.87

1/18/2006 7:37:30 AM Linearity Check 0.01 0 6.1

1/18/2006 7:38:00 AM Linearity Check 0.01 -0.05 6.13

1/18/2006 7:38:30 AM Linearity Check 0.01 -0.05 6.13

1/18/2006 7:39:00 AM Linearity Check -0.05 0 6.07

1/18/2006 7:39:30 AM Linearity Check 0.01 -0.05 6.08

1/18/2006 7:40:00 AM Linearity Check -0.05 -0.05 5.57

1/18/2006 7:40:30 AM Linearity Check 0.62 0.09 3.39

1/18/2006 7:41:00 AM Linearity Check 0.14 -0.05 3.09

1/18/2006 7:41:30 AM Linearity Check 0.01 0 3.12

1/18/2006 7:42:00 AM Linearity Check 0.01 0 3.08

1/18/2006 7:42:30 AM Linearity Check 8.25 5.86 1.08

1/18/2006 7:43:00 AM Linearity Check 12.53 11.08 0.06

1/18/2006 7:43:30 AM Linearity Check 12.65 11.03 -0.02

1/18/2006 7:44:00 AM Linearity Check 12.59 11.03 0.16

1/18/2006 7:44:30 AM Linearity Check 12.53 9.08 2.74

1/18/2006 7:45:00 AM Linearity Check 12.65 8.64 2.75

1/18/2006 7:45:30 AM Linearity Check 12.83 10.89 0.25

1/18/2006 7:46:00 AM - Span 12.59 10.99 0.03

1/18/2006 7:46:30 AM - Span 12.59 11.03 0.02

1/18/2006 7:47:00 AM - Span 12.59 11.03 0.09

1/18/2006 7:47:30 AM - Span 4.29 4.93 3.89

1/18/2006 7:48:00 AM - Span 0.08 0.14 6.01

1/18/2006 7:48:30 AM - Span 0.01 0.05 6.18

1/18/2006 7:49:00 AM - Span 0.01 0.05 6.17

1/18/2006 7:49:30 AM - Span 0.01 0 6.19

1/18/2006 7:50:00 AM - Span -0.05 0 6.2

1/18/2006 7:50:30 AM - Span 0.01 0.05 6.22

1/18/2006 7:51:00 AM - Span 0.01 0.05 6.16

1/18/2006 7:51:30 AM - Span 8.99 5.37 4.36

Page 1 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 7:52:00 AM - Span 12.28 8.59 3.66

1/18/2006 7:52:30 AM - Span 12.34 8.69 3.61

1/18/2006 7:53:00 AM - Span 12.28 8.69 3.66

1/18/2006 7:53:30 AM - Span 12.28 8.74 4.03

1/18/2006 7:54:00 AM - Span 12.28 8.69 3.76

1/18/2006 7:54:30 AM - Span 12.34 8.69 3.76

1/18/2006 7:55:00 AM - Span 12.28 8.64 3.74

1/18/2006 7:55:30 AM - Span 12.34 8.69 3.62

1/18/2006 7:56:00 AM - Span 12.41 8.64 3.39

1/18/2006 7:56:30 AM - Span 12.41 8.59 3.31

1/18/2006 7:57:00 AM - Span 12.34 8.64 3.39

1/18/2006 7:57:30 AM - Span 12.34 8.59 3.44

1/18/2006 7:58:00 AM - Span 12.34 8.54 3.4

1/18/2006 7:58:30 AM - Span 12.34 8.49 3.33

1/18/2006 7:59:00 AM - Span 12.34 8.49 3.43

1/18/2006 7:59:30 AM - Span 12.34 8.54 3.57

1/18/2006 8:00:00 AM - Span 12.34 8.49 3.58

1/18/2006 8:00:30 AM - Span 12.34 8.49 3.6

1/18/2006 8:01:00 AM - Span 12.34 8.49 3.59

1/18/2006 8:01:30 AM - Span 12.41 8.49 3.49

1/18/2006 8:02:00 AM - Span 12.41 8.45 3.45

1/18/2006 8:02:30 AM Run 1 - 1 12.47 8.45 3.36

1/18/2006 8:03:00 AM Run 1 - 1 12.47 8.4 3.28

1/18/2006 8:03:30 AM Run 1 - 1 12.53 8.4 3.28

1/18/2006 8:04:00 AM Run 1 - 1 12.53 8.45 3.31

1/18/2006 8:04:30 AM Run 1 - 1 12.53 8.45 3.22

1/18/2006 8:05:00 AM Run 1 - 1 12.47 8.4 3.23

1/18/2006 8:05:30 AM Run 1 - 1 12.53 8.4 3.2

1/18/2006 8:06:00 AM Run 1 - 1 12.47 8.4 3.14

1/18/2006 8:06:30 AM Run 1 - 1 12.47 8.35 3.2

1/18/2006 8:07:00 AM Run 1 - 1 12.53 8.35 3.15

1/18/2006 8:07:30 AM Run 1 - 1 12.53 8.4 3.21

1/18/2006 8:08:00 AM Run 1 - 1 12.47 8.3 3.23

1/18/2006 8:08:30 AM Run 1 - 1 12.53 8.3 3.25

1/18/2006 8:09:00 AM Run 1 - 1 12.53 8.3 3.21

1/18/2006 8:09:30 AM Run 1 - 1 12.53 8.3 3.15

1/18/2006 8:10:00 AM Run 1 - 1 12.53 8.3 3.12

1/18/2006 8:10:30 AM 12.53 8.35 3.15

1/18/2006 8:11:00 AM 12.53 8.35 3.11

1/18/2006 8:11:30 AM 12.59 8.35 3.1

Page 2 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 8:12:00 AM 12.53 8.35 3.13

1/18/2006 8:12:30 AM 12.53 8.4 3.17

1/18/2006 8:13:00 AM 12.53 8.4 3.16

1/18/2006 8:13:30 AM 12.53 8.4 3.04

1/18/2006 8:14:00 AM 12.59 8.35 2.94

1/18/2006 8:14:30 AM 12.53 8.35 3.05

1/18/2006 8:15:00 AM 12.59 8.4 3.1

1/18/2006 8:15:30 AM 12.53 8.35 3.05

1/18/2006 8:16:00 AM 12.59 8.4 2.97

1/18/2006 8:16:30 AM 12.59 8.35 2.96

1/18/2006 8:17:00 AM 12.59 8.4 3.06

1/18/2006 8:17:30 AM 12.53 8.35 3.05

1/18/2006 8:18:00 AM 12.53 8.35 2.94

1/18/2006 8:18:30 AM 12.53 8.3 3.02

1/18/2006 8:19:00 AM 12.53 8.3 3.05

1/18/2006 8:19:30 AM 12.59 8.3 2.99

1/18/2006 8:20:00 AM 12.53 8.3 2.94

1/18/2006 8:20:30 AM 12.59 8.35 2.98

1/18/2006 8:21:00 AM 12.53 8.35 3.12

1/18/2006 8:21:30 AM 12.53 8.35 3.12

1/18/2006 8:22:00 AM 12.59 8.4 3.11

1/18/2006 8:22:30 AM 12.53 8.35 3.04

1/18/2006 8:23:00 AM 12.53 8.35 3.13

1/18/2006 8:23:30 AM 12.53 8.35 3.05

1/18/2006 8:24:00 AM 12.53 8.35 3.08

1/18/2006 8:24:30 AM 12.53 8.35 2.75

1/18/2006 8:25:00 AM 12.53 8.4 2.72

1/18/2006 8:25:30 AM 12.53 8.3 3.13

1/18/2006 8:26:00 AM 12.53 8.3 3.17

1/18/2006 8:26:30 AM 12.53 8.35 3.06

1/18/2006 8:27:00 AM 12.59 8.35 3.03

1/18/2006 8:27:30 AM 12.53 8.35 3.03

1/18/2006 8:28:00 AM 12.53 8.35 3

1/18/2006 8:28:30 AM 12.47 8.3 3.11

1/18/2006 8:29:00 AM 12.47 8.3 3.29

1/18/2006 8:29:30 AM 12.47 8.35 3.36

1/18/2006 8:30:00 AM 12.47 8.35 3.42

1/18/2006 8:30:30 AM 12.47 8.35 3.42

1/18/2006 8:31:00 AM 12.53 8.35 3.36

1/18/2006 8:31:30 AM 12.47 8.35 3.3

Page 3 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 8:32:00 AM 12.47 8.35 3.45

1/18/2006 8:32:30 AM 12.41 8.35 3.51

1/18/2006 8:33:00 AM 12.41 8.3 3.58

1/18/2006 8:33:30 AM 12.47 8.35 3.57

1/18/2006 8:34:00 AM 12.47 8.3 3.58

1/18/2006 8:34:30 AM 12.41 8.35 3.58

1/18/2006 8:35:00 AM 12.47 8.35 3.71

1/18/2006 8:35:30 AM 12.41 8.3 3.7

1/18/2006 8:36:00 AM 12.41 8.3 3.58

1/18/2006 8:36:30 AM 12.41 8.3 3.64

1/18/2006 8:37:00 AM 12.41 8.3 3.6

1/18/2006 8:37:30 AM 12.41 8.25 3.52

1/18/2006 8:38:00 AM 12.41 8.2 3.74

1/18/2006 8:38:30 AM 12.41 8.25 3.74

1/18/2006 8:39:00 AM 12.41 8.2 3.75

1/18/2006 8:39:30 AM 12.41 8.2 3.78

1/18/2006 8:40:00 AM 12.41 8.2 3.78

1/18/2006 8:40:30 AM 12.41 8.2 3.78

1/18/2006 8:41:00 AM 12.47 8.2 3.71

1/18/2006 8:41:30 AM 12.47 8.25 3.66

1/18/2006 8:42:00 AM 12.47 8.3 3.55

1/18/2006 8:42:30 AM 12.41 8.25 3.59

1/18/2006 8:43:00 AM 12.47 8.2 3.56

1/18/2006 8:43:30 AM 12.47 8.25 3.58

1/18/2006 8:44:00 AM 12.47 8.25 3.56

1/18/2006 8:44:30 AM 12.47 8.25 3.53

1/18/2006 8:45:00 AM 12.47 8.25 3.46

1/18/2006 8:45:30 AM 12.53 8.25 3.41

1/18/2006 8:46:00 AM 12.53 8.25 3.37

1/18/2006 8:46:30 AM 12.53 8.25 3.21

1/18/2006 8:47:00 AM 12.53 8.25 3.16

1/18/2006 8:47:30 AM 12.53 8.25 3.21

1/18/2006 8:48:00 AM 12.53 8.25 3.08

1/18/2006 8:48:30 AM 12.53 8.2 3.22

1/18/2006 8:49:00 AM 12.59 8.2 3.26

1/18/2006 8:49:30 AM 12.59 8.25 3.1

1/18/2006 8:50:00 AM 12.59 8.25 3.14

1/18/2006 8:50:30 AM 12.59 8.3 3.17

1/18/2006 8:51:00 AM 12.59 8.3 3.13

1/18/2006 8:51:30 AM 12.59 8.3 3.2

Page 4 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 8:52:00 AM 12.59 8.3 3.22

1/18/2006 8:52:30 AM 12.59 8.3 3.16

1/18/2006 8:53:00 AM 12.59 8.3 3.12

1/18/2006 8:53:30 AM 12.59 8.35 3.03

1/18/2006 8:54:00 AM 12.59 8.3 3.02

1/18/2006 8:54:30 AM 12.59 8.35 3.1

1/18/2006 8:55:00 AM 12.59 8.35 3.04

1/18/2006 8:55:30 AM 12.59 8.3 2.97

1/18/2006 8:56:00 AM 12.59 8.35 2.99

1/18/2006 8:56:30 AM 12.59 8.35 3.12

1/18/2006 8:57:00 AM 12.59 8.35 3.03

1/18/2006 8:57:30 AM 12.53 8.35 3.15

1/18/2006 8:58:00 AM 12.59 8.3 3.11

1/18/2006 8:58:30 AM 12.59 8.25 3.09

1/18/2006 8:59:00 AM 12.59 8.3 3.12

1/18/2006 8:59:30 AM 12.59 8.25 3.11

1/18/2006 9:00:00 AM 12.59 8.3 3.01

1/18/2006 9:00:30 AM 12.59 8.35 3.02

1/18/2006 9:01:00 AM 12.53 8.35 3.15

1/18/2006 9:01:30 AM 12.59 8.35 3.14

1/18/2006 9:02:00 AM 12.59 8.35 3.12

1/18/2006 9:02:30 AM 12.59 8.35 3.12

1/18/2006 9:03:00 AM 12.59 8.35 3.11

1/18/2006 9:03:30 AM 12.59 8.35 3.07

1/18/2006 9:04:00 AM 12.59 8.35 3.08

1/18/2006 9:04:30 AM 12.65 8.35 3.05

1/18/2006 9:05:00 AM 12.65 8.35 2.95

1/18/2006 9:05:30 AM 12.59 8.35 2.99

1/18/2006 9:06:00 AM 12.59 8.35 3.09

1/18/2006 9:06:30 AM 12.53 8.35 3.13

1/18/2006 9:07:00 AM 12.53 8.35 3.12

1/18/2006 9:07:30 AM 12.59 8.4 3.12

1/18/2006 9:08:00 AM 12.59 8.4 3.13

1/18/2006 9:08:30 AM 12.53 8.35 3.18

1/18/2006 9:09:00 AM 12.53 8.35 3.14

1/18/2006 9:09:30 AM 12.59 8.4 3.07

1/18/2006 9:10:00 AM 12.59 8.4 3.03

1/18/2006 9:10:30 AM 12.53 8.4 3.07

1/18/2006 9:11:00 AM 12.53 8.4 3.17

1/18/2006 9:11:30 AM 12.53 8.45 3.26

Page 5 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 9:12:00 AM 12.53 8.45 3.39

1/18/2006 9:12:30 AM 12.47 8.45 3.48

1/18/2006 9:13:00 AM 12.47 8.49 3.52

1/18/2006 9:13:30 AM 12.47 8.49 3.56

1/18/2006 9:14:00 AM 12.47 8.45 3.59

1/18/2006 9:14:30 AM 12.47 8.45 3.62

1/18/2006 9:15:00 AM 12.41 8.45 3.75

1/18/2006 9:15:30 AM 12.41 8.49 3.81

1/18/2006 9:16:00 AM 12.41 8.49 3.89

1/18/2006 9:16:30 AM 12.34 8.49 3.98

1/18/2006 9:17:00 AM 12.41 8.49 4.11

1/18/2006 9:17:30 AM 12.34 8.49 4.19

1/18/2006 9:18:00 AM 12.34 8.49 4.19

1/18/2006 9:18:30 AM 12.28 8.45 4.29

1/18/2006 9:19:00 AM 12.28 8.4 4.19

1/18/2006 9:19:30 AM 12.34 8.45 4.25

1/18/2006 9:20:00 AM 12.28 8.49 4.34

1/18/2006 9:20:30 AM 12.28 8.45 4.43

1/18/2006 9:21:00 AM 12.28 8.49 4.49

1/18/2006 9:21:30 AM 12.28 8.49 4.58

1/18/2006 9:22:00 AM 12.28 8.49 4.57

1/18/2006 9:22:30 AM 12.22 8.45 4.57

1/18/2006 9:23:00 AM 12.28 8.45 4.52

1/18/2006 9:23:30 AM 12.22 8.4 4.49

1/18/2006 9:24:00 AM 12.28 8.35 4.35

1/18/2006 9:24:30 AM 12.28 8.4 4.37

1/18/2006 9:25:00 AM 12.28 8.4 3.88

1/18/2006 9:25:30 AM 12.28 8.4 4.21

1/18/2006 9:26:00 AM 12.28 8.4 4.5

1/18/2006 9:26:30 AM 12.34 8.4 4.47

1/18/2006 9:27:00 AM 12.34 8.35 4.46

1/18/2006 9:27:30 AM 12.28 8.35 4.39

1/18/2006 9:28:00 AM 12.34 8.35 4.34

1/18/2006 9:28:30 AM 12.28 8.35 4.19

1/18/2006 9:29:00 AM 12.41 8.35 4.14

1/18/2006 9:29:30 AM 12.34 8.35 3.96

1/18/2006 9:30:00 AM 12.34 8.4 3.97

1/18/2006 9:30:30 AM 12.41 8.4 3.9

1/18/2006 9:31:00 AM 12.34 8.4 3.83

1/18/2006 9:31:30 AM 12.41 8.45 3.91

Page 6 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 9:32:00 AM 12.41 8.45 3.72

1/18/2006 9:32:30 AM 12.41 8.45 3.67

1/18/2006 9:33:00 AM 12.47 8.45 3.65

1/18/2006 9:33:30 AM 12.41 8.45 3.61

1/18/2006 9:34:00 AM 12.47 8.45 3.51

1/18/2006 9:34:30 AM 12.41 8.4 3.7

1/18/2006 9:35:00 AM 12.41 8.45 3.8

1/18/2006 9:35:30 AM 12.34 8.49 3.75

1/18/2006 9:36:00 AM 12.41 8.49 3.7

1/18/2006 9:36:30 AM 12.41 8.49 3.64

1/18/2006 9:37:00 AM 12.41 8.54 3.68

1/18/2006 9:37:30 AM 12.41 8.54 3.67

1/18/2006 9:38:00 AM 12.34 8.49 3.82

1/18/2006 9:38:30 AM 12.41 8.49 3.9

1/18/2006 9:39:00 AM 12.34 8.49 3.7

1/18/2006 9:39:30 AM 12.34 8.49 3.77

1/18/2006 9:40:00 AM 12.34 8.49 3.75

1/18/2006 9:40:30 AM 12.41 8.54 3.83

1/18/2006 9:41:00 AM 12.41 8.54 3.9

1/18/2006 9:41:30 AM 12.41 8.54 3.77

1/18/2006 9:42:00 AM 12.41 8.59 3.88

1/18/2006 9:42:30 AM 12.34 8.59 3.79

1/18/2006 9:43:00 AM 12.34 8.59 3.8

1/18/2006 9:43:30 AM 12.34 8.59 3.96

1/18/2006 9:44:00 AM 12.34 8.59 4.05

1/18/2006 9:44:30 AM 12.34 8.59 4.08

1/18/2006 9:45:00 AM 12.34 8.64 4.03

1/18/2006 9:45:30 AM 12.28 8.59 3.97

1/18/2006 9:46:00 AM 12.34 8.64 4.03

1/18/2006 9:46:30 AM 12.34 8.59 3.89

1/18/2006 9:47:00 AM 12.34 8.64 3.92

1/18/2006 9:47:30 AM 12.34 8.64 3.98

1/18/2006 9:48:00 AM 12.34 8.64 4.07

1/18/2006 9:48:30 AM 12.34 8.64 4.13

1/18/2006 9:49:00 AM 12.28 8.59 4.23

1/18/2006 9:49:30 AM 12.28 8.59 4.18

1/18/2006 9:50:00 AM 12.28 8.59 4.1

1/18/2006 9:50:30 AM 12.22 8.59 4.19

1/18/2006 9:51:00 AM 12.22 8.59 4.32

1/18/2006 9:51:30 AM 12.22 8.64 4.46

Page 7 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 9:52:00 AM 12.22 8.64 4.61

1/18/2006 9:52:30 AM 12.22 8.64 4.42

1/18/2006 9:53:00 AM 12.22 8.59 4.35

1/18/2006 9:53:30 AM 12.22 8.64 4.43

1/18/2006 9:54:00 AM 12.22 8.69 4.41

1/18/2006 9:54:30 AM 12.22 8.59 4.48

1/18/2006 9:55:00 AM 12.22 8.59 4.58

1/18/2006 9:55:30 AM 12.16 8.54 4.5

1/18/2006 9:56:00 AM 12.22 8.59 4.56

1/18/2006 9:56:30 AM 12.16 8.59 4.75

1/18/2006 9:57:00 AM 12.16 8.64 4.76

1/18/2006 9:57:30 AM 12.22 8.59 4.49

1/18/2006 9:58:00 AM 12.22 8.49 4.6

1/18/2006 9:58:30 AM 12.22 8.54 4.69

1/18/2006 9:59:00 AM 12.16 8.54 4.51

1/18/2006 9:59:30 AM 12.22 8.49 4.64

1/18/2006 10:00:00 AM 12.22 8.45 4.62

1/18/2006 10:00:30 AM 12.22 8.49 4.64

1/18/2006 10:01:00 AM 12.28 8.49 4.51

1/18/2006 10:01:30 AM 12.22 8.49 4.46

1/18/2006 10:02:00 AM 12.16 8.49 4.42

1/18/2006 10:02:30 AM 12.22 8.49 4.51

1/18/2006 10:03:00 AM 12.22 8.54 4.46

1/18/2006 10:03:30 AM 12.22 8.49 4.43

1/18/2006 10:04:00 AM 12.28 8.49 4.37

1/18/2006 10:04:30 AM 12.22 8.45 4.29

1/18/2006 10:05:00 AM 12.28 8.4 4.33

1/18/2006 10:05:30 AM 12.28 8.49 4.42

1/18/2006 10:06:00 AM 12.28 8.45 4.44

1/18/2006 10:06:30 AM 12.28 8.45 4.34

1/18/2006 10:07:00 AM 12.28 8.45 4.31

1/18/2006 10:07:30 AM 12.28 8.45 4.17

1/18/2006 10:08:00 AM 12.34 8.49 4.17

1/18/2006 10:08:30 AM 12.28 8.45 4.19

1/18/2006 10:09:00 AM 12.34 8.45 4.09

1/18/2006 10:09:30 AM 12.41 8.49 3.84

1/18/2006 10:10:00 AM 12.41 8.54 3.84

1/18/2006 10:10:30 AM 12.41 8.54 3.73

1/18/2006 10:11:00 AM 12.47 8.49 3.63

1/18/2006 10:11:30 AM 12.47 8.49 3.62

Page 8 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 10:12:00 AM 12.41 8.49 3.62

1/18/2006 10:12:30 AM 12.47 8.54 3.59

1/18/2006 10:13:00 AM 12.41 8.54 3.62

1/18/2006 10:13:30 AM 12.47 8.49 3.59

1/18/2006 10:14:00 AM 12.47 8.54 3.5

1/18/2006 10:14:30 AM 12.41 8.59 3.58

1/18/2006 10:15:00 AM 12.47 8.59 3.59

1/18/2006 10:15:30 AM 12.47 8.59 3.64

1/18/2006 10:16:00 AM 12.47 8.59 3.66

1/18/2006 10:16:30 AM 12.47 8.59 3.66

1/18/2006 10:17:00 AM 12.47 8.64 3.74

1/18/2006 10:17:30 AM 12.41 8.69 3.7

1/18/2006 10:18:00 AM 12.41 8.64 3.72

1/18/2006 10:18:30 AM 12.41 8.64 3.71

1/18/2006 10:19:00 AM 12.41 8.59 3.64

1/18/2006 10:19:30 AM 12.47 8.59 3.69

1/18/2006 10:20:00 AM 12.47 8.59 3.62

1/18/2006 10:20:30 AM 12.41 8.59 3.74

1/18/2006 10:21:00 AM 12.41 8.59 3.79

1/18/2006 10:21:30 AM 12.41 8.59 3.78

1/18/2006 10:22:00 AM 12.41 8.59 3.86

1/18/2006 10:22:30 AM 12.41 8.59 3.88

1/18/2006 10:23:00 AM 12.34 8.69 3.91

1/18/2006 10:23:30 AM 12.34 8.69 3.95

1/18/2006 10:24:00 AM 12.34 8.69 3.95

1/18/2006 10:24:30 AM 12.34 8.64 3.85

1/18/2006 10:25:00 AM 12.34 8.69 3.94

1/18/2006 10:25:30 AM 12.28 8.64 3.34

1/18/2006 10:26:00 AM 12.34 8.64 3.65

1/18/2006 10:26:30 AM 12.34 8.59 3.97

1/18/2006 10:27:00 AM 12.34 8.64 4.05

1/18/2006 10:27:30 AM 12.28 8.59 4.29

1/18/2006 10:28:00 AM 12.28 8.59 4.21

1/18/2006 10:28:30 AM 12.34 8.64 4.14

1/18/2006 10:29:00 AM 12.28 8.64 4.1

1/18/2006 10:29:30 AM 12.34 8.59 4.16

1/18/2006 10:30:00 AM 12.34 8.59 4.25

1/18/2006 10:30:30 AM 12.28 8.59 4.24

1/18/2006 10:31:00 AM 12.34 8.59 4.14

1/18/2006 10:31:30 AM 12.28 8.54 4.07

Page 9 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 10:32:00 AM 12.34 8.59 3.99

1/18/2006 10:32:30 AM 12.28 8.64 3.99

1/18/2006 10:33:00 AM 12.34 8.64 4.06

1/18/2006 10:33:30 AM 12.34 8.59 4.01

1/18/2006 10:34:00 AM 12.34 8.59 4.25

1/18/2006 10:34:30 AM 12.28 8.59 4.19

1/18/2006 10:35:00 AM 12.28 8.59 4.32

1/18/2006 10:35:30 AM 12.22 8.59 4.45

1/18/2006 10:36:00 AM 12.22 8.54 4.35

1/18/2006 10:36:30 AM 12.28 8.59 4.26

1/18/2006 10:37:00 AM 12.22 8.59 4.26

1/18/2006 10:37:30 AM 12.22 8.59 4.19

1/18/2006 10:38:00 AM 12.28 8.59 4.26

1/18/2006 10:38:30 AM 12.22 8.59 4.32

1/18/2006 10:39:00 AM 12.22 8.54 4.39

1/18/2006 10:39:30 AM 12.28 8.59 4.37

1/18/2006 10:40:00 AM 12.28 8.59 4.47

1/18/2006 10:40:30 AM 12.22 8.54 4.32

1/18/2006 10:41:00 AM 12.28 8.54 4.19

1/18/2006 10:41:30 AM 12.28 8.54 4.19

1/18/2006 10:42:00 AM 12.28 8.54 4.14

1/18/2006 10:42:30 AM 12.28 8.54 4.08

1/18/2006 10:43:00 AM 12.34 8.54 4.03

1/18/2006 10:43:30 AM 12.34 8.45 4.02

1/18/2006 10:44:00 AM 12.34 8.4 3.95

1/18/2006 10:44:30 AM 12.34 8.45 3.97

1/18/2006 10:45:00 AM 12.41 8.35 3.94

1/18/2006 10:45:30 AM 12.34 8.4 3.93

1/18/2006 10:46:00 AM 12.34 8.4 3.81

1/18/2006 10:46:30 AM 12.41 8.45 3.86

1/18/2006 10:47:00 AM 12.34 8.45 3.86

1/18/2006 10:47:30 AM 12.34 8.45 3.82

1/18/2006 10:48:00 AM 12.34 8.45 3.94

1/18/2006 10:48:30 AM 12.34 8.4 4

1/18/2006 10:49:00 AM 12.41 8.4 3.98

1/18/2006 10:49:30 AM 12.34 8.45 3.9

1/18/2006 10:50:00 AM 12.34 8.49 3.94

1/18/2006 10:50:30 AM 12.28 8.49 4.03

1/18/2006 10:51:00 AM 12.34 8.54 4.09

1/18/2006 10:51:30 AM 12.28 8.49 4.12

Page 10 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 10:52:00 AM 12.28 8.49 4.18

1/18/2006 10:52:30 AM 12.28 8.49 4.01

1/18/2006 10:53:00 AM 12.34 8.54 4.01

1/18/2006 10:53:30 AM 12.28 8.49 3.98

1/18/2006 10:54:00 AM 12.34 8.49 4.15

1/18/2006 10:54:30 AM 12.34 8.54 4.02

1/18/2006 10:55:00 AM 12.34 8.54 4.04

1/18/2006 10:55:30 AM 12.28 8.54 4.01

1/18/2006 10:56:00 AM 12.34 8.54 3.94

1/18/2006 10:56:30 AM 12.34 8.49 3.9

1/18/2006 10:57:00 AM 12.34 8.54 4.03

1/18/2006 10:57:30 AM 12.34 8.49 4.11

1/18/2006 10:58:00 AM 12.34 8.49 4.09

1/18/2006 10:58:30 AM 12.34 8.45 4.1

1/18/2006 10:59:00 AM 12.34 8.49 4.07

1/18/2006 10:59:30 AM 12.28 8.49 4

1/18/2006 11:00:00 AM 12.34 8.49 4.08

1/18/2006 11:00:30 AM 12.34 8.54 4.02

1/18/2006 11:01:00 AM 12.34 8.59 4.21

1/18/2006 11:01:30 AM 12.28 8.59 4.21

1/18/2006 11:02:00 AM 12.28 8.54 4.21

1/18/2006 11:02:30 AM 12.28 8.59 4.15

1/18/2006 11:03:00 AM 12.28 8.59 4.24

1/18/2006 11:03:30 AM 12.28 8.59 4.25

1/18/2006 11:04:00 AM 12.28 8.54 4.08

1/18/2006 11:04:30 AM 12.34 8.49 3.95

1/18/2006 11:05:00 AM 12.34 8.54 3.86

1/18/2006 11:05:30 AM 12.34 8.54 3.92

1/18/2006 11:06:00 AM 12.28 8.59 4.05

1/18/2006 11:06:30 AM 12.34 8.54 4.08

1/18/2006 11:07:00 AM 12.28 8.54 4.02

1/18/2006 11:07:30 AM 12.28 8.54 3.89

1/18/2006 11:08:00 AM 12.34 8.49 3.96

1/18/2006 11:08:30 AM 12.34 8.49 3.86

1/18/2006 11:09:00 AM 12.34 8.49 3.83

1/18/2006 11:09:30 AM 12.34 8.49 3.87

1/18/2006 11:10:00 AM 12.34 8.49 3.85

1/18/2006 11:10:30 AM 12.34 8.54 3.86

1/18/2006 11:11:00 AM 12.34 8.54 4

1/18/2006 11:11:30 AM 12.34 8.54 3.94

Page 11 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 11:12:00 AM 12.34 8.54 3.89

1/18/2006 11:12:30 AM 12.34 8.49 3.9

1/18/2006 11:13:00 AM 12.34 8.54 4.01

1/18/2006 11:13:30 AM 12.28 8.49 3.98

1/18/2006 11:14:00 AM 12.28 8.49 3.95

1/18/2006 11:14:30 AM 12.34 8.49 3.86

1/18/2006 11:15:00 AM 12.34 8.49 3.94

1/18/2006 11:15:30 AM 12.34 8.49 3.87

1/18/2006 11:16:00 AM 12.34 8.49 3.94

1/18/2006 11:16:30 AM 12.34 8.49 3.97

1/18/2006 11:17:00 AM 12.34 8.49 3.96

1/18/2006 11:17:30 AM 12.34 8.49 3.84

1/18/2006 11:18:00 AM 12.34 8.49 3.83

1/18/2006 11:18:30 AM 12.34 8.45 3.99

1/18/2006 11:19:00 AM 12.34 8.49 3.96

1/18/2006 11:19:30 AM 12.34 8.45 3.96

1/18/2006 11:20:00 AM 12.28 8.54 4.06

1/18/2006 11:20:30 AM 12.34 8.49 4.14

1/18/2006 11:21:00 AM 12.34 8.54 4

1/18/2006 11:21:30 AM 12.34 8.49 4.01

1/18/2006 11:22:00 AM 12.34 8.49 4.04

1/18/2006 11:22:30 AM 12.34 8.49 4.05

1/18/2006 11:23:00 AM 12.34 8.54 4.03

1/18/2006 11:23:30 AM 12.28 8.54 4.04

1/18/2006 11:24:00 AM 12.34 8.49 4.09

1/18/2006 11:24:30 AM 12.34 8.54 4.04

1/18/2006 11:25:00 AM 12.28 8.54 4.05

1/18/2006 11:25:30 AM 12.28 8.59 4.13

1/18/2006 11:26:00 AM 12.28 8.54 3.6

1/18/2006 11:26:30 AM 12.34 8.54 3.82

1/18/2006 11:27:00 AM 12.28 8.54 4.13

1/18/2006 11:27:30 AM 12.34 8.54 4.03

1/18/2006 11:28:00 AM 12.34 8.54 4.25

1/18/2006 11:28:30 AM 12.34 8.54 4.19

1/18/2006 11:29:00 AM 12.28 8.49 4.15

1/18/2006 11:29:30 AM 12.28 8.54 4.06

1/18/2006 11:30:00 AM 12.34 8.49 4.03

1/18/2006 11:30:30 AM 12.34 8.45 4.05

1/18/2006 11:31:00 AM 12.34 8.54 4.08

1/18/2006 11:31:30 AM 12.28 8.54 4.06

Page 12 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 11:32:00 AM 12.28 8.59 4.06

1/18/2006 11:32:30 AM 12.28 8.54 3.99

1/18/2006 11:33:00 AM 12.28 8.54 4.1

1/18/2006 11:33:30 AM 12.28 8.54 4.05

1/18/2006 11:34:00 AM 12.28 8.49 4.15

1/18/2006 11:34:30 AM 12.28 8.49 3.96

1/18/2006 11:35:00 AM 12.34 8.49 3.93

1/18/2006 11:35:30 AM 12.34 8.54 4.07

1/18/2006 11:36:00 AM 12.34 8.49 4.09

1/18/2006 11:36:30 AM 12.28 8.54 4.1

1/18/2006 11:37:00 AM 12.22 8.54 4.13

1/18/2006 11:37:30 AM 12.28 8.54 4.14

1/18/2006 11:38:00 AM 12.28 8.49 4.08

1/18/2006 11:38:30 AM 12.28 8.54 4.05

1/18/2006 11:39:00 AM 12.28 8.45 4.1

1/18/2006 11:39:30 AM 12.34 8.45 4.05

1/18/2006 11:40:00 AM 12.34 8.45 4

1/18/2006 11:40:30 AM 12.28 8.49 4

1/18/2006 11:41:00 AM 12.34 8.49 3.95

1/18/2006 11:41:30 AM 12.28 8.49 4.09

1/18/2006 11:42:00 AM 12.28 8.49 4.12

1/18/2006 11:42:30 AM 12.28 8.45 3.96

1/18/2006 11:43:00 AM 12.34 8.49 3.89

1/18/2006 11:43:30 AM 12.34 8.49 3.9

1/18/2006 11:44:00 AM 12.28 8.49 3.99

1/18/2006 11:44:30 AM 12.34 8.45 4.03

1/18/2006 11:45:00 AM 12.34 8.49 4.18

1/18/2006 11:45:30 AM 12.28 8.54 4.35

1/18/2006 11:46:00 AM 12.28 8.49 4.26

1/18/2006 11:46:30 AM 12.34 8.49 4.15

1/18/2006 11:47:00 AM 12.28 8.54 4.29

1/18/2006 11:47:30 AM 12.28 8.49 4.22

1/18/2006 11:48:00 AM 12.28 8.45 4.15

1/18/2006 11:48:30 AM 12.28 8.45 4.22

1/18/2006 11:49:00 AM 12.28 8.45 4.24

1/18/2006 11:49:30 AM 12.28 8.45 4

1/18/2006 11:50:00 AM 12.34 8.4 4.04

1/18/2006 11:50:30 AM 12.34 8.49 4.11

1/18/2006 11:51:00 AM 12.34 8.49 4.18

1/18/2006 11:51:30 AM 12.28 8.49 4.13

Page 13 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 11:52:00 AM 12.22 8.49 4.2

1/18/2006 11:52:30 AM 12.28 8.49 4.3

1/18/2006 11:53:00 AM 12.28 8.45 4.26

1/18/2006 11:53:30 AM 12.22 8.45 4.24

1/18/2006 11:54:00 AM 12.22 8.45 4.31

1/18/2006 11:54:30 AM 12.28 8.49 4.54

1/18/2006 11:55:00 AM 12.22 8.49 4.42

1/18/2006 11:55:30 AM 12.22 8.49 4.47

1/18/2006 11:56:00 AM 12.22 8.49 4.44

1/18/2006 11:56:30 AM 12.28 8.45 4.41

1/18/2006 11:57:00 AM 12.22 8.49 4.31

1/18/2006 11:57:30 AM 12.22 8.49 4.5

1/18/2006 11:58:00 AM 12.28 8.49 4.37

1/18/2006 11:58:30 AM 12.28 8.4 4.12

1/18/2006 11:59:00 AM 12.28 8.4 4.21

1/18/2006 11:59:30 AM 12.28 8.4 4.28

1/18/2006 12:00:00 PM 12.22 8.4 4.15

1/18/2006 12:00:30 PM 12.28 8.45 4.26

1/18/2006 12:01:00 PM 12.22 8.45 4.32

1/18/2006 12:01:30 PM 12.22 8.45 4.08

1/18/2006 12:02:00 PM 12.22 8.45 4.25

1/18/2006 12:02:30 PM 12.22 8.49 4.23

1/18/2006 12:03:00 PM 12.22 8.4 4.24

1/18/2006 12:03:30 PM 12.22 8.45 4.2

1/18/2006 12:04:00 PM 12.22 8.45 4.31

1/18/2006 12:04:30 PM 12.22 8.49 4.37

1/18/2006 12:05:00 PM 12.22 8.45 4.31

1/18/2006 12:05:30 PM 12.22 8.49 4.39

1/18/2006 12:06:00 PM 12.22 8.49 4.28

1/18/2006 12:06:30 PM 12.28 8.49 4.2

1/18/2006 12:07:00 PM 12.28 8.49 4.24

1/18/2006 12:07:30 PM 12.28 8.45 4.16

1/18/2006 12:08:00 PM 12.28 8.4 4.01

1/18/2006 12:08:30 PM 12.22 8.4 4.1

1/18/2006 12:09:00 PM 12.28 8.45 4.15

1/18/2006 12:09:30 PM 12.28 8.49 4.1

1/18/2006 12:10:00 PM 12.28 8.49 4.08

1/18/2006 12:10:30 PM 12.22 8.54 4.09

1/18/2006 12:11:00 PM 12.28 8.49 4.1

1/18/2006 12:11:30 PM 12.34 8.49 4.06

Page 14 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 12:12:00 PM 12.34 8.45 3.99

1/18/2006 12:12:30 PM 12.28 8.45 4.08

1/18/2006 12:13:00 PM Run 1 - 1 12.28 8.45 4.11

1/18/2006 12:13:30 PM Run 1 - 1 12.28 8.45 4.11

1/18/2006 12:14:00 PM Run 1 - 1 12.28 8.45 4.14

1/18/2006 12:14:30 PM Run 1 - 1 12.28 8.49 4.15

1/18/2006 12:15:00 PM Run 1 - 1 12.34 8.45 4.12

1/18/2006 12:15:30 PM Run 1 - 1 12.28 8.49 4.13

1/18/2006 12:16:00 PM Run 1 - 1 12.28 8.49 4.09

1/18/2006 12:16:30 PM Run 1 - 1 12.28 8.49 4.07

1/18/2006 12:17:00 PM Run 1 - 1 12.22 8.49 4.16

1/18/2006 12:17:30 PM Run 1 - 1 12.28 8.49 4.09

1/18/2006 12:18:00 PM Run 1 - 1 12.34 8.49 4.09

1/18/2006 12:18:30 PM Run 1 - 1 12.28 8.45 4.13

1/18/2006 12:19:00 PM Run 1 - 1 12.28 8.45 4.15

1/18/2006 12:19:30 PM Run 1 - 1 12.28 8.49 4.2

1/18/2006 12:20:00 PM Run 1 - 1 12.28 8.49 4.3

1/18/2006 12:20:30 PM Run 1 - 1 12.34 8.49 4.28

1/18/2006 12:21:00 PM Run 1 - 1 12.28 8.49 4.28

1/18/2006 12:21:30 PM Run 1 - 1 12.28 8.49 4.18

1/18/2006 12:22:00 PM Run 1 - 1 12.34 8.49 4.16

1/18/2006 12:22:30 PM Run 1 - 1 12.28 8.59 4.25

1/18/2006 12:23:00 PM Run 1 - 1 12.28 8.59 4.18

1/18/2006 12:23:30 PM Run 1 - 1 12.34 8.49 4.11

1/18/2006 12:24:00 PM Run 1 - 1 12.34 8.49 4.06

1/18/2006 12:24:30 PM Run 1 - 1 12.34 8.49 4.03

1/18/2006 12:25:00 PM Run 1 - 1 12.34 8.49 3.99

1/18/2006 12:25:30 PM Run 1 - 1 12.34 8.49 4.21

1/18/2006 12:26:00 PM Run 1 - 1 12.34 8.49 4.26

1/18/2006 12:26:30 PM Run 1 - 1 12.28 8.49 3.64

1/18/2006 12:27:00 PM Run 1 - 1 12.34 8.49 3.68

1/18/2006 12:27:30 PM Run 1 - 1 12.28 8.49 4.09

1/18/2006 12:28:00 PM Run 1 - 1 12.34 8.49 4.3

1/18/2006 12:28:30 PM Run 1 - 1 12.22 8.49 4.35

1/18/2006 12:29:00 PM Run 1 - 1 12.22 8.49 4.34

1/18/2006 12:29:30 PM Run 1 - 1 12.34 8.49 4.3

1/18/2006 12:30:00 PM Run 1 - 1 12.28 8.49 4.31

1/18/2006 12:30:30 PM Run 1 - 1 12.34 8.49 4.2

1/18/2006 12:31:00 PM Run 1 - 1 12.34 8.49 4.2

1/18/2006 12:31:30 PM Run 1 - 1 12.28 8.49 4.24

Page 15 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 12:32:00 PM Run 1 - 1 12.28 8.54 4.27

1/18/2006 12:32:30 PM Run 1 - 1 12.34 8.54 4.29

1/18/2006 12:33:00 PM Run 1 - 1 12.28 8.49 4.05

1/18/2006 12:33:30 PM Run 1 - 1 12.34 8.49 4.12

1/18/2006 12:34:00 PM Run 1 - 1 12.34 8.49 4.07

1/18/2006 12:34:30 PM Run 1 - 1 12.34 8.49 4.1

1/18/2006 12:35:00 PM Run 1 - 1 12.34 8.54 4.2

1/18/2006 12:35:30 PM Run 1 - 1 12.34 8.49 4.13

1/18/2006 12:36:00 PM Run 1 - 1 12.34 8.49 4.16

1/18/2006 12:36:30 PM Run 1 - 1 12.34 8.49 4.05

1/18/2006 12:37:00 PM Run 1 - 1 12.28 8.54 4.15

1/18/2006 12:37:30 PM Run 1 - 1 12.34 8.54 4.14

1/18/2006 12:38:00 PM Run 1 - 1 12.28 8.49 4.12

1/18/2006 12:38:30 PM Run 1 - 1 12.28 8.54 4.19

1/18/2006 12:39:00 PM Run 1 - 1 12.28 8.45 4.19

1/18/2006 12:39:30 PM Run 1 - 1 12.28 8.49 4.05

1/18/2006 12:40:00 PM Run 1 - 1 12.28 8.45 4

1/18/2006 12:40:30 PM Run 1 - 1 12.28 8.49 4.12

1/18/2006 12:41:00 PM Run 1 - 1 12.34 8.45 4.13

1/18/2006 12:41:30 PM Run 1 - 1 12.28 8.49 4.13

1/18/2006 12:42:00 PM Run 1 - 1 12.28 8.49 4.27

1/18/2006 12:42:30 PM Run 1 - 1 12.28 8.49 4.3

1/18/2006 12:43:00 PM Run 1 - 1 12.28 8.49 4.23

1/18/2006 12:43:30 PM Run 1 - 1 12.28 8.49 4.16

1/18/2006 12:44:00 PM Run 1 - 1 12.22 8.54 4.2

1/18/2006 12:44:30 PM Run 1 - 1 12.22 8.54 4.17

1/18/2006 12:45:00 PM Run 1 - 1 12.28 8.54 4.36

1/18/2006 12:45:30 PM Run 1 - 1 12.22 8.54 4.42

1/18/2006 12:46:00 PM Run 1 - 1 12.28 8.54 4.31

1/18/2006 12:46:30 PM Run 1 - 1 12.22 8.49 4.23

1/18/2006 12:47:00 PM Run 1 - 1 12.22 8.49 4.23

1/18/2006 12:47:30 PM Run 1 - 1 12.22 8.49 4.22

1/18/2006 12:48:00 PM Run 1 - 1 12.28 8.45 4.3

1/18/2006 12:48:30 PM Run 1 - 1 12.22 8.4 4.2

1/18/2006 12:49:00 PM Run 1 - 1 12.28 8.45 4.13

1/18/2006 12:49:30 PM Run 1 - 1 12.22 8.45 4.24

1/18/2006 12:50:00 PM Run 1 - 1 12.28 8.49 4.17

1/18/2006 12:50:30 PM Run 1 - 1 12.22 8.49 4.33

1/18/2006 12:51:00 PM Run 1 - 1 12.28 8.49 4.24

1/18/2006 12:51:30 PM Run 1 - 1 12.28 8.49 4.4

Page 16 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 12:52:00 PM Run 1 - 1 12.22 8.49 4.42

1/18/2006 12:52:30 PM Run 1 - 1 12.28 8.45 4.39

1/18/2006 12:53:00 PM Run 1 - 1 12.28 8.45 4.22

1/18/2006 12:53:30 PM Run 1 - 1 12.22 8.45 4.32

1/18/2006 12:54:00 PM Run 1 - 1 12.28 8.45 4.26

1/18/2006 12:54:30 PM Run 1 - 1 12.28 8.45 4.13

1/18/2006 12:55:00 PM Run 1 - 1 12.28 8.49 4.27

1/18/2006 12:55:30 PM Run 1 - 1 12.28 8.49 4.34

1/18/2006 12:56:00 PM Run 1 - 1 12.28 8.54 4.32

1/18/2006 12:56:30 PM Run 1 - 1 12.22 8.54 4.35

1/18/2006 12:57:00 PM Run 1 - 1 12.22 8.49 4.22

1/18/2006 12:57:30 PM Run 1 - 1 12.28 8.45 4.23

1/18/2006 12:58:00 PM Run 1 - 1 12.28 8.45 4.08

1/18/2006 12:58:30 PM Run 1 - 1 12.34 8.4 4.06

1/18/2006 12:59:00 PM Run 1 - 1 12.28 8.4 4.08

1/18/2006 12:59:30 PM Run 1 - 1 12.28 8.45 4.16

1/18/2006 1:00:00 PM Run 1 - 1 12.22 8.45 4.27

1/18/2006 1:00:30 PM Run 1 - 1 12.28 8.45 4.11

1/18/2006 1:01:00 PM Run 1 - 1 12.28 8.49 4.14

1/18/2006 1:01:30 PM Run 1 - 1 12.28 8.45 4.23

1/18/2006 1:02:00 PM Run 1 - 1 12.22 8.45 4.25

1/18/2006 1:02:30 PM Run 1 - 1 12.22 8.45 4.22

1/18/2006 1:03:00 PM Run 1 - 1 12.22 8.45 4.14

1/18/2006 1:03:30 PM Run 1 - 1 12.28 8.45 4.08

1/18/2006 1:04:00 PM Run 1 - 1 12.28 8.45 4.29

1/18/2006 1:04:30 PM Run 1 - 1 12.28 8.45 4.25

1/18/2006 1:05:00 PM Run 1 - 1 12.28 8.45 4.26

1/18/2006 1:05:30 PM Run 1 - 1 12.28 8.45 4.29

1/18/2006 1:06:00 PM Run 1 - 1 12.22 8.45 4.29

1/18/2006 1:06:30 PM Run 1 - 1 12.28 8.45 4.27

1/18/2006 1:07:00 PM Run 1 - 1 12.28 8.45 4.2

1/18/2006 1:07:30 PM Run 1 - 1 12.28 8.45 4.11

1/18/2006 1:08:00 PM Run 1 - 1 12.28 8.45 4.21

1/18/2006 1:08:30 PM Run 1 - 1 12.28 8.45 4.28

1/18/2006 1:09:00 PM Run 1 - 1 12.28 8.45 4.11

1/18/2006 1:09:30 PM Run 1 - 1 12.28 8.4 4.03

1/18/2006 1:10:00 PM Run 1 - 1 12.22 8.45 4.25

1/18/2006 1:10:30 PM Run 1 - 1 12.28 8.4 4.31

1/18/2006 1:11:00 PM Run 1 - 1 12.28 8.4 4.2

1/18/2006 1:11:30 PM Run 1 - 1 12.22 8.45 4.19

Page 17 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 1:12:00 PM Run 1 - 1 12.28 8.4 4.32

1/18/2006 1:12:30 PM Run 1 - 1 12.22 8.45 4.34

1/18/2006 1:13:00 PM 12.22 8.45 4.53

1/18/2006 1:13:30 PM 12.1 8.45 4.46

1/18/2006 1:14:00 PM 11.86 9.62 0.72

1/18/2006 1:14:30 PM 12.59 10.99 0.31

1/18/2006 1:15:00 PM 12.59 11.03 0.29

1/18/2006 1:15:30 PM 12.59 11.03 0.29

1/18/2006 1:16:00 PM 12.59 11.03 0.3

1/18/2006 1:16:30 PM 12.59 10.99 0.3

1/18/2006 1:17:00 PM - ZERO 12.53 10.99 0.3

1/18/2006 1:17:30 PM - ZERO 11.98 10.99 1.98

1/18/2006 1:18:00 PM - ZERO 1.48 2.34 5.75

1/18/2006 1:18:30 PM - ZERO 0.01 0.09 6.4

1/18/2006 1:19:00 PM - ZERO 0.01 0 6.39

1/18/2006 1:19:30 PM - Span 0.01 0 6.41

1/18/2006 1:20:00 PM - Span -0.05 0 6.01

1/18/2006 1:20:30 PM - Span 10.21 6.35 4.49

1/18/2006 1:21:00 PM - Span 12.16 8.4 4.32

1/18/2006 1:21:30 PM - Span 12.22 8.4 4.1

1/18/2006 1:22:00 PM - Span 12.22 8.4 4.16

1/18/2006 1:22:30 PM - Span 12.22 8.4 4.32

1/18/2006 1:23:00 PM - Span 12.22 8.45 4.14

1/18/2006 1:23:30 PM Run 2 - 1 12.28 8.49 4.2

1/18/2006 1:24:00 PM Run 2 - 1 12.22 8.45 4.15

1/18/2006 1:24:30 PM Run 2 - 1 12.22 8.45 4.03

1/18/2006 1:25:00 PM Run 2 - 1 12.22 8.45 4.06

1/18/2006 1:25:30 PM Run 2 - 1 12.22 8.45 4.1

1/18/2006 1:26:00 PM Run 2 - 1 12.28 8.45 4.02

1/18/2006 1:26:30 PM Run 2 - 1 12.28 8.45 3.98

1/18/2006 1:27:00 PM Run 2 - 1 12.28 8.45 3.47

1/18/2006 1:27:30 PM Run 2 - 1 12.28 8.45 3.65

1/18/2006 1:28:00 PM Run 2 - 1 12.28 8.45 4

1/18/2006 1:28:30 PM Run 2 - 1 12.28 8.45 4.17

1/18/2006 1:29:00 PM Run 2 - 1 12.28 8.45 4.01

1/18/2006 1:29:30 PM Run 2 - 1 12.28 8.49 3.99

1/18/2006 1:30:00 PM Run 2 - 1 12.28 8.45 4.13

1/18/2006 1:30:30 PM Run 2 - 1 12.28 8.49 4.22

1/18/2006 1:31:00 PM Run 2 - 1 12.28 8.49 4.15

1/18/2006 1:31:30 PM Run 2 - 1 12.28 8.49 4.32

Page 18 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 1:32:00 PM Run 2 - 1 12.22 8.49 4.33

1/18/2006 1:32:30 PM Run 2 - 1 12.22 8.49 4.2

1/18/2006 1:33:00 PM Run 2 - 1 12.22 8.49 4.12

1/18/2006 1:33:30 PM Run 2 - 1 12.28 8.49 4.04

1/18/2006 1:34:00 PM Run 2 - 1 12.28 8.49 4.17

1/18/2006 1:34:30 PM Run 2 - 1 12.28 8.49 4.22

1/18/2006 1:35:00 PM Run 2 - 1 12.34 8.49 4.15

1/18/2006 1:35:30 PM Run 2 - 1 12.28 8.49 4.06

1/18/2006 1:36:00 PM Run 2 - 1 12.28 8.45 4.05

1/18/2006 1:36:30 PM Run 2 - 1 12.34 8.45 4.07

1/18/2006 1:37:00 PM Run 2 - 1 12.28 8.45 4.15

1/18/2006 1:37:30 PM Run 2 - 1 12.28 8.45 4.11

1/18/2006 1:38:00 PM Run 2 - 1 12.34 8.45 4.16

1/18/2006 1:38:30 PM Run 2 - 1 12.28 8.4 4.22

1/18/2006 1:39:00 PM Run 2 - 1 12.28 8.4 4.11

1/18/2006 1:39:30 PM Run 2 - 1 12.34 8.4 4

1/18/2006 1:40:00 PM Run 2 - 1 12.28 8.45 4.1

1/18/2006 1:40:30 PM Run 2 - 1 12.28 8.45 4.1

1/18/2006 1:41:00 PM Run 2 - 1 12.28 8.45 4.19

1/18/2006 1:41:30 PM Run 2 - 1 12.34 8.45 4.24

1/18/2006 1:42:00 PM Run 2 - 1 12.28 8.49 4.25

1/18/2006 1:42:30 PM Run 2 - 1 12.28 8.49 4.13

1/18/2006 1:43:00 PM Run 2 - 1 12.28 8.49 4.03

1/18/2006 1:43:30 PM Run 2 - 1 12.28 8.49 4.07

1/18/2006 1:44:00 PM Run 2 - 1 12.28 8.45 4

1/18/2006 1:44:30 PM Run 2 - 1 12.34 8.49 4.08

1/18/2006 1:45:00 PM Run 2 - 1 12.34 8.45 4.14

1/18/2006 1:45:30 PM Run 2 - 1 12.34 8.49 4.12

1/18/2006 1:46:00 PM Run 2 - 1 12.28 8.49 4.16

1/18/2006 1:46:30 PM Run 2 - 1 12.28 8.45 4.17

1/18/2006 1:47:00 PM Run 2 - 1 12.28 8.49 4.24

1/18/2006 1:47:30 PM Run 2 - 1 12.28 8.45 4.08

1/18/2006 1:48:00 PM Run 2 - 1 12.28 8.49 4.15

1/18/2006 1:48:30 PM Run 2 - 1 12.28 8.45 4.11

1/18/2006 1:49:00 PM Run 2 - 1 12.28 8.4 3.96

1/18/2006 1:49:30 PM Run 2 - 1 12.28 8.4 4.06

1/18/2006 1:50:00 PM Run 2 - 1 12.28 8.45 4.1

1/18/2006 1:50:30 PM Run 2 - 1 12.28 8.45 4.1

1/18/2006 1:51:00 PM Run 2 - 1 12.28 8.45 4.04

1/18/2006 1:51:30 PM Run 2 - 1 12.34 8.49 4.03

Page 19 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 1:52:00 PM Run 2 - 1 12.28 8.45 4.05

1/18/2006 1:52:30 PM Run 2 - 1 12.34 8.49 4.1

1/18/2006 1:53:00 PM Run 2 - 1 12.28 8.45 4.08

1/18/2006 1:53:30 PM Run 2 - 1 12.34 8.49 3.92

1/18/2006 1:54:00 PM Run 2 - 1 12.34 8.45 4.05

1/18/2006 1:54:30 PM Run 2 - 1 12.28 8.49 4.1

1/18/2006 1:55:00 PM Run 2 - 1 12.34 8.49 4.19

1/18/2006 1:55:30 PM Run 2 - 1 12.34 8.49 4.18

1/18/2006 1:56:00 PM Run 2 - 1 12.28 8.49 4.12

1/18/2006 1:56:30 PM Run 2 - 1 12.28 8.49 4.06

1/18/2006 1:57:00 PM Run 2 - 1 12.34 8.49 4.1

1/18/2006 1:57:30 PM Run 2 - 1 12.28 8.49 4.04

1/18/2006 1:58:00 PM Run 2 - 1 12.34 8.49 4.02

1/18/2006 1:58:30 PM Run 2 - 1 12.28 8.49 3.98

1/18/2006 1:59:00 PM Run 2 - 1 12.28 8.4 3.94

1/18/2006 1:59:30 PM Run 2 - 1 12.28 8.45 4.05

1/18/2006 2:00:00 PM Run 2 - 1 12.28 8.45 4.11

1/18/2006 2:00:30 PM Run 2 - 1 12.34 8.49 4.08

1/18/2006 2:01:00 PM Run 2 - 1 12.28 8.49 3.95

1/18/2006 2:01:30 PM Run 2 - 1 12.28 8.49 4.11

1/18/2006 2:02:00 PM Run 2 - 1 12.34 8.49 4.02

1/18/2006 2:02:30 PM Run 2 - 1 12.28 8.45 3.9

1/18/2006 2:03:00 PM Run 2 - 1 12.34 8.49 4.03

1/18/2006 2:03:30 PM Run 2 - 1 12.28 8.49 4.26

1/18/2006 2:04:00 PM Run 2 - 1 12.28 8.49 4.16

1/18/2006 2:04:30 PM Run 2 - 1 12.28 8.45 4.03

1/18/2006 2:05:00 PM Run 2 - 1 12.28 8.45 4.01

1/18/2006 2:05:30 PM Run 2 - 1 12.28 8.45 3.99

1/18/2006 2:06:00 PM Run 2 - 1 12.28 8.49 3.98

1/18/2006 2:06:30 PM Run 2 - 1 12.28 8.45 3.96

1/18/2006 2:07:00 PM Run 2 - 1 12.28 8.45 4.09

1/18/2006 2:07:30 PM Run 2 - 1 12.28 8.45 4.07

1/18/2006 2:08:00 PM Run 2 - 1 12.34 8.49 3.91

1/18/2006 2:08:30 PM Run 2 - 1 12.28 8.45 3.99

1/18/2006 2:09:00 PM Run 2 - 1 12.28 8.4 4.09

1/18/2006 2:09:30 PM Run 2 - 1 12.28 8.4 4.05

1/18/2006 2:10:00 PM Run 2 - 1 12.28 8.45 4.03

1/18/2006 2:10:30 PM Run 2 - 1 12.28 8.45 3.93

1/18/2006 2:11:00 PM Run 2 - 1 12.34 8.45 3.91

1/18/2006 2:11:30 PM Run 2 - 1 12.34 8.45 3.99

Page 20 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 2:12:00 PM Run 2 - 1 12.28 8.45 4.03

1/18/2006 2:12:30 PM Run 2 - 1 12.34 8.49 4.01

1/18/2006 2:13:00 PM Run 2 - 1 12.34 8.45 4

1/18/2006 2:13:30 PM Run 2 - 1 12.34 8.45 4.06

1/18/2006 2:14:00 PM Run 2 - 1 12.34 8.45 4.04

1/18/2006 2:14:30 PM Run 2 - 1 12.28 8.49 4.16

1/18/2006 2:15:00 PM Run 2 - 1 12.34 8.49 4.03

1/18/2006 2:15:30 PM Run 2 - 1 12.34 8.45 4.19

1/18/2006 2:16:00 PM Run 2 - 1 12.34 8.45 4.13

1/18/2006 2:16:30 PM Run 2 - 1 12.34 8.49 4.18

1/18/2006 2:17:00 PM Run 2 - 1 12.34 8.45 4.17

1/18/2006 2:17:30 PM Run 2 - 1 12.28 8.49 4.06

1/18/2006 2:18:00 PM Run 2 - 1 12.28 8.49 4.09

1/18/2006 2:18:30 PM Run 2 - 1 12.34 8.45 4

1/18/2006 2:19:00 PM Run 2 - 1 12.28 8.45 4.08

1/18/2006 2:19:30 PM Run 2 - 1 12.34 8.45 4.09

1/18/2006 2:20:00 PM Run 2 - 1 12.34 8.45 4.1

1/18/2006 2:20:30 PM Run 2 - 1 12.34 8.4 3.95

1/18/2006 2:21:00 PM Run 2 - 1 12.34 8.45 4.08

1/18/2006 2:21:30 PM Run 2 - 1 12.34 8.45 4

1/18/2006 2:22:00 PM Run 2 - 1 12.28 8.49 4.16

1/18/2006 2:22:30 PM Run 2 - 1 12.28 8.45 4.21

1/18/2006 2:23:00 PM Run 2 - 1 12.28 8.45 4.01

1/18/2006 2:23:30 PM 12.34 8.49 4.09

1/18/2006 2:24:00 PM 12.34 8.49 4.08

1/18/2006 2:24:30 PM 11.43 9.23 1.14

1/18/2006 2:25:00 PM 12.53 10.99 0.29

1/18/2006 2:25:30 PM 12.53 10.99 0.27

1/18/2006 2:26:00 PM 12.53 10.99 0.28

1/18/2006 2:26:30 PM 12.59 11.03 0.28

1/18/2006 2:27:00 PM 12.53 10.99 0.28

1/18/2006 2:27:30 PM 12.53 10.99 0.29

1/18/2006 2:28:00 PM 12.53 10.99 0.29

1/18/2006 2:28:30 PM - ZERO 12.53 11.03 0.3

1/18/2006 2:29:00 PM - ZERO 11.92 10.99 1.55

1/18/2006 2:29:30 PM - ZERO 1.23 2.15 5.56

1/18/2006 2:30:00 PM - ZERO 0.01 0.09 6.38

1/18/2006 2:30:30 PM - ZERO 0.01 0.05 6.4

1/18/2006 2:31:00 PM - ZERO 0.01 0.05 6.4

1/18/2006 2:31:30 PM - ZERO 0.01 0 6.39

Page 21 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 2:32:00 PM - ZERO -0.05 0 6.4

1/18/2006 2:32:30 PM - ZERO -0.05 0 6.39

1/18/2006 2:33:00 PM - ZERO 0.01 0.05 6.4

1/18/2006 2:33:30 PM - ZERO -0.05 0 6.38

1/18/2006 2:34:00 PM - ZERO -0.05 0 6.38

1/18/2006 2:34:30 PM - Span -0.05 0 6.39

1/18/2006 2:35:00 PM - Span 2.64 0.78 5.53

1/18/2006 2:35:30 PM - Span 11.67 7.52 4.22

1/18/2006 2:36:00 PM - Span 12.28 8.4 4.14

1/18/2006 2:36:30 PM - Span 12.22 8.4 4.15

1/18/2006 2:37:00 PM - Span 12.22 8.4 4.17

1/18/2006 2:37:30 PM - Span 12.22 8.4 4.2

1/18/2006 2:38:00 PM - Span 12.28 8.4 4.21

1/18/2006 2:38:30 PM - Span 12.22 8.35 4.19

1/18/2006 2:39:00 PM - Span 12.16 8.35 4.25

1/18/2006 2:39:30 PM - Span 12.22 8.35 4.07

1/18/2006 2:40:00 PM - Span 12.22 8.35 4.06

1/18/2006 2:40:30 PM - Span 12.22 8.4 4.08

1/18/2006 2:41:00 PM - Span 12.28 8.35 4.02

1/18/2006 2:41:30 PM - Span 12.28 8.4 4.21

1/18/2006 2:42:00 PM - Span 12.28 8.45 4.29

1/18/2006 2:42:30 PM Run 3 - 1 12.28 8.4 4.16

1/18/2006 2:43:00 PM Run 3 - 1 12.28 8.4 4.16

1/18/2006 2:43:30 PM Run 3 - 1 12.28 8.35 4.23

1/18/2006 2:44:00 PM Run 3 - 1 12.34 8.4 4.11

1/18/2006 2:44:30 PM Run 3 - 1 12.34 8.4 4.08

1/18/2006 2:45:00 PM Run 3 - 1 12.28 8.4 4.01

1/18/2006 2:45:30 PM Run 3 - 1 12.34 8.4 3.98

1/18/2006 2:46:00 PM Run 3 - 1 12.34 8.4 4.02

1/18/2006 2:46:30 PM Run 3 - 1 12.34 8.4 3.94

1/18/2006 2:47:00 PM Run 3 - 1 12.34 8.45 4.02

1/18/2006 2:47:30 PM Run 3 - 1 12.34 8.49 4.05

1/18/2006 2:48:00 PM Run 3 - 1 12.34 8.49 4.09

1/18/2006 2:48:30 PM Run 3 - 1 12.28 8.45 4.06

1/18/2006 2:49:00 PM Run 3 - 1 12.28 8.4 3.98

1/18/2006 2:49:30 PM Run 3 - 1 12.34 8.4 3.92

1/18/2006 2:50:00 PM Run 3 - 1 12.34 8.4 3.81

1/18/2006 2:50:30 PM Run 3 - 1 12.34 8.4 3.94

1/18/2006 2:51:00 PM Run 3 - 1 12.34 8.45 3.85

1/18/2006 2:51:30 PM Run 3 - 1 12.34 8.4 3.85

Page 22 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 2:52:00 PM Run 3 - 1 12.34 8.4 3.96

1/18/2006 2:52:30 PM Run 3 - 1 12.34 8.35 3.91

1/18/2006 2:53:00 PM Run 3 - 1 12.41 8.4 4

1/18/2006 2:53:30 PM Run 3 - 1 12.34 8.4 4.07

1/18/2006 2:54:00 PM Run 3 - 1 12.34 8.4 4.14

1/18/2006 2:54:30 PM Run 3 - 1 12.34 8.45 4.09

1/18/2006 2:55:00 PM Run 3 - 1 12.41 8.4 3.91

1/18/2006 2:55:30 PM Run 3 - 1 12.34 8.45 4.02

1/18/2006 2:56:00 PM Run 3 - 1 12.34 8.45 4.23

1/18/2006 2:56:30 PM Run 3 - 1 12.28 8.45 4.11

1/18/2006 2:57:00 PM Run 3 - 1 12.28 8.45 4.03

1/18/2006 2:57:30 PM Run 3 - 1 12.34 8.45 4.1

1/18/2006 2:58:00 PM Run 3 - 1 12.34 8.45 4.11

1/18/2006 2:58:30 PM Run 3 - 1 12.34 8.4 4.09

1/18/2006 2:59:00 PM Run 3 - 1 12.28 8.4 4.07

1/18/2006 2:59:30 PM Run 3 - 1 12.34 8.35 3.86

1/18/2006 3:00:00 PM Run 3 - 1 12.34 8.35 3.78

1/18/2006 3:00:30 PM Run 3 - 1 12.41 8.35 3.87

1/18/2006 3:01:00 PM Run 3 - 1 12.34 8.4 3.96

1/18/2006 3:01:30 PM Run 3 - 1 12.34 8.4 3.93

1/18/2006 3:02:00 PM Run 3 - 1 12.34 8.45 4

1/18/2006 3:02:30 PM Run 3 - 1 12.34 8.45 3.89

1/18/2006 3:03:00 PM Run 3 - 1 12.34 8.45 4.01

1/18/2006 3:03:30 PM Run 3 - 1 12.34 8.49 4.07

1/18/2006 3:04:00 PM Run 3 - 1 12.28 8.45 4.17

1/18/2006 3:04:30 PM Run 3 - 1 12.34 8.45 4.21

1/18/2006 3:05:00 PM Run 3 - 1 12.34 8.45 4.18

1/18/2006 3:05:30 PM Run 3 - 1 12.34 8.45 4.12

1/18/2006 3:06:00 PM Run 3 - 1 12.34 8.45 4.03

1/18/2006 3:06:30 PM Run 3 - 1 12.34 8.45 4.06

1/18/2006 3:07:00 PM Run 3 - 1 12.34 8.4 3.95

1/18/2006 3:07:30 PM Run 3 - 1 12.34 8.4 3.96

1/18/2006 3:08:00 PM Run 3 - 1 12.34 8.35 3.88

1/18/2006 3:08:30 PM Run 3 - 1 12.34 8.4 3.81

1/18/2006 3:09:00 PM Run 3 - 1 12.34 8.4 3.89

1/18/2006 3:09:30 PM Run 3 - 1 12.34 8.35 3.91

1/18/2006 3:10:00 PM Run 3 - 1 12.34 8.4 3.96

1/18/2006 3:10:30 PM Run 3 - 1 12.41 8.4 3.91

1/18/2006 3:11:00 PM Run 3 - 1 12.34 8.45 3.97

1/18/2006 3:11:30 PM Run 3 - 1 12.41 8.4 3.92

Page 23 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 3:12:00 PM Run 3 - 1 12.34 8.45 3.95

1/18/2006 3:12:30 PM Run 3 - 1 12.41 8.45 3.96

1/18/2006 3:13:00 PM Run 3 - 1 12.34 8.45 4.01

1/18/2006 3:13:30 PM Run 3 - 1 12.34 8.49 4.1

1/18/2006 3:14:00 PM Run 3 - 1 12.34 8.49 3.93

1/18/2006 3:14:30 PM Run 3 - 1 12.34 8.45 3.87

1/18/2006 3:15:00 PM Run 3 - 1 12.28 8.45 3.9

1/18/2006 3:15:30 PM Run 3 - 1 12.34 8.45 3.91

1/18/2006 3:16:00 PM Run 3 - 1 12.28 8.45 4.1

1/18/2006 3:16:30 PM Run 3 - 1 12.34 8.45 4.12

1/18/2006 3:17:00 PM Run 3 - 1 12.34 8.45 4.08

1/18/2006 3:17:30 PM Run 3 - 1 12.34 8.45 3.92

1/18/2006 3:18:00 PM Run 3 - 1 12.34 8.45 3.92

1/18/2006 3:18:30 PM Run 3 - 1 12.34 8.45 3.9

1/18/2006 3:19:00 PM Run 3 - 1 12.28 8.45 3.93

1/18/2006 3:19:30 PM Run 3 - 1 12.28 8.4 3.93

1/18/2006 3:20:00 PM Run 3 - 1 12.34 8.4 3.93

1/18/2006 3:20:30 PM Run 3 - 1 12.34 8.4 3.75

1/18/2006 3:21:00 PM Run 3 - 1 12.41 8.4 3.83

1/18/2006 3:21:30 PM Run 3 - 1 12.34 8.4 3.82

1/18/2006 3:22:00 PM Run 3 - 1 12.41 8.45 3.86

1/18/2006 3:22:30 PM Run 3 - 1 12.41 8.45 3.83

1/18/2006 3:23:00 PM Run 3 - 1 12.41 8.45 3.81

1/18/2006 3:23:30 PM Run 3 - 1 12.34 8.45 3.9

1/18/2006 3:24:00 PM Run 3 - 1 12.34 8.45 3.81

1/18/2006 3:24:30 PM Run 3 - 1 12.34 8.45 3.85

1/18/2006 3:25:00 PM Run 3 - 1 12.34 8.45 3.8

1/18/2006 3:25:30 PM Run 3 - 1 12.34 8.45 3.91

1/18/2006 3:26:00 PM Run 3 - 1 12.34 8.45 4.05

1/18/2006 3:26:30 PM Run 3 - 1 12.34 8.4 4.01

1/18/2006 3:27:00 PM Run 3 - 1 12.34 8.4 3.9

1/18/2006 3:27:30 PM Run 3 - 1 12.28 8.4 3.97

1/18/2006 3:28:00 PM Run 3 - 1 12.34 8.45 3.48

1/18/2006 3:28:30 PM Run 3 - 1 12.34 8.4 3.51

1/18/2006 3:29:00 PM Run 3 - 1 12.28 8.4 3.91

1/18/2006 3:29:30 PM Run 3 - 1 12.34 8.4 3.91

1/18/2006 3:30:00 PM Run 3 - 1 12.34 8.45 4.02

1/18/2006 3:30:30 PM Run 3 - 1 12.28 8.4 4.13

1/18/2006 3:31:00 PM Run 3 - 1 12.34 8.4 3.91

1/18/2006 3:31:30 PM Run 3 - 1 12.34 8.35 4

Page 24 of 25
LabView Run Log

Date Time Status O2 (%) CO2 (%) CO (PPM)

1/18/2006 3:32:00 PM Run 3 - 1 12.28 8.4 3.91

1/18/2006 3:32:30 PM Run 3 - 1 12.34 8.4 3.98

1/18/2006 3:33:00 PM Run 3 - 1 12.28 8.4 4.05

1/18/2006 3:33:30 PM Run 3 - 1 12.28 8.4 4.15

1/18/2006 3:34:00 PM Run 3 - 1 12.28 8.4 4.06

1/18/2006 3:34:30 PM Run 3 - 1 12.34 8.4 3.85

1/18/2006 3:35:00 PM Run 3 - 1 12.41 8.4 3.87

1/18/2006 3:35:30 PM Run 3 - 1 12.34 8.45 3.99

1/18/2006 3:36:00 PM Run 3 - 1 12.34 8.45 4.08

1/18/2006 3:36:30 PM Run 3 - 1 12.28 8.49 4.18

1/18/2006 3:37:00 PM Run 3 - 1 12.34 8.45 4.05

1/18/2006 3:37:30 PM Run 3 - 1 12.28 8.45 4.08

1/18/2006 3:38:00 PM Run 3 - 1 12.34 8.45 4.09

1/18/2006 3:38:30 PM Run 3 - 1 12.34 8.45 3.95

1/18/2006 3:39:00 PM Run 3 - 1 12.28 8.4 3.92

1/18/2006 3:39:30 PM Run 3 - 1 12.28 8.4 3.86

1/18/2006 3:40:00 PM Run 3 - 1 12.28 8.4 3.89

1/18/2006 3:40:30 PM Run 3 - 1 12.34 8.45 3.86

1/18/2006 3:41:00 PM Run 3 - 1 12.34 8.45 3.99

1/18/2006 3:41:30 PM Run 3 - 1 12.34 8.4 3.89

1/18/2006 3:42:00 PM Run 3 - 1 12.34 8.4 3.83

1/18/2006 3:42:30 PM 12.34 8.45 3.86

1/18/2006 3:43:00 PM 10.09 7.47 3.11

1/18/2006 3:43:30 PM 12.41 10.69 0.54

1/18/2006 3:44:00 PM 12.59 10.99 0.28

1/18/2006 3:44:30 PM - ZERO 12.53 10.99 0.27

1/18/2006 3:45:00 PM - ZERO 8.01 8.2 2.51

1/18/2006 3:45:30 PM - ZERO 0.26 0.58 5.94

1/18/2006 3:46:00 PM - ZERO 0.01 0.05 6.43

1/18/2006 3:46:30 PM - Span 0.01 0.05 6.4

Page 25 of 25
CYLINDER GAS CERTIFICATES 




APPENDIX B 

TURBINE DATA 
Plant Information Database Query Results

Plant Information Source: polk-1pisrv

Start Time: 1/18/2006 12:12

End Time: 1/18/2006 15:42

Time Interval: 1 Min

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

Run Average: 175.0169586 6878.19847 60.9636799 5.19140375

18-Jan-06 12:12:00 173.9932404 6914.50537 61.7775192 5.35535908

18-Jan-06 12:13:00 174.7501984 6926.29688 62.0808868 5.31999731

18-Jan-06 12:14:00 174.5588684 6917.8457 61.9268913 5.28463507

18-Jan-06 12:15:00 174.9079132 6922.11426 61.8818932 5.24927282

18-Jan-06 12:16:00 174.9543762 6897.15527 62.0863113 5.21391058

18-Jan-06 12:17:00 175.3853912 6908.20557 61.9335709 5.17854834

18-Jan-06 12:18:00 175.1585999 6931.09424 62.0175781 5.14318657

18-Jan-06 12:19:00 175.9933777 7017.23242 61.5967178 5.10782433

18-Jan-06 12:20:00 175.3030548 6967.55176 62.1426544 5.07246208

18-Jan-06 12:21:00 174.7611237 6940.41748 62.2979202 5.06424189

18-Jan-06 12:22:00 176.057785 6823.90332 62.3272743 5.08316326

18-Jan-06 12:23:00 174.4391174 6765.75977 61.4808617 5.10208464

18-Jan-06 12:24:00 174.4540405 6787.49365 61.3323631 5.12100601

18-Jan-06 12:25:00 174.4689636 6810.59424 61.2141762 5.13992739

18-Jan-06 12:26:00 174.4838867 6833.69482 61.6718788 5.14295816

18-Jan-06 12:27:00 175.3782806 6865.64502 62.111515 5.13009739

18-Jan-06 12:28:00 175.0710907 6948.94141 61.8088303 5.11723661

18-Jan-06 12:29:00 176.3258972 6867.50879 61.8088303 5.10437584

18-Jan-06 12:30:00 175.0547791 6850.6416 61.9016342 5.09151506

18-Jan-06 12:31:00 175.6758118 6834.7373 61.6737175 5.13924885

18-Jan-06 12:32:00 174.7147522 6829.42041 61.4458008 5.2436676

18-Jan-06 12:33:00 174.1577301 6823.26318 61.2178802 5.29404402

18-Jan-06 12:34:00 174.2936249 6809.40576 61.7278404 5.29037762

18-Jan-06 12:35:00 174.643692 6812.52246 61.5419083 5.28671122

18-Jan-06 12:36:00 174.2169342 6813.88232 62.0280151 5.28304482

18-Jan-06 12:37:00 174.3813477 6820.92285 62.061348 5.27937841

18-Jan-06 12:38:00 174.6652832 6902.70508 61.8672104 5.27571249

18-Jan-06 12:39:00 174.7204437 6861.68311 61.6394386 5.27204609

18-Jan-06 12:40:00 174.3116302 6856.08105 61.7357712 5.26837969

18-Jan-06 12:41:00 174.917099 6863.41455 61.7266998 5.26471329

18-Jan-06 12:42:00 175.0638885 6863.12109 61.6428604 5.26104689

18-Jan-06 12:43:00 175.1095123 6900.56738 61.8481865 5.25738049

Page 1 of 6
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

18-Jan-06 12:44:00 175.6387329 6886.56934 62.0535088 5.25371456

18-Jan-06 12:45:00 176.3822937 6973.27783 62.0708313 5.25004816

18-Jan-06 12:46:00 176.2565155 6975.34375 61.9941483 5.24638176

18-Jan-06 12:47:00 175.1668549 6994.11182 61.9174652 5.24271536

18-Jan-06 12:48:00 174.3897705 7005.29834 61.8407822 5.24033785

18-Jan-06 12:49:00 174.333313 6968.08057 62.5158768 5.23916531

18-Jan-06 12:50:00 174.8615417 6952.92725 62.716877 5.23799324

18-Jan-06 12:51:00 174.9147034 6938.67578 62.2047615 5.2368207

18-Jan-06 12:52:00 174.9402466 6925.51807 62.3600235 5.23564863

18-Jan-06 12:53:00 174.2243195 6928.90674 62.2734604 5.23447609

18-Jan-06 12:54:00 174.8390503 6921.02295 62.2913437 5.23330402

18-Jan-06 12:55:00 175.5738983 6920.14014 62.2583084 5.23213196

18-Jan-06 12:56:00 174.5343018 6908.13135 62.0436707 5.23095942

18-Jan-06 12:57:00 174.4504089 6923.55029 61.3709488 5.22978735

18-Jan-06 12:58:00 174.4202271 6957.65137 61.6157417 5.22861481

18-Jan-06 12:59:00 174.6122589 6920.96484 62.1219521 5.22744274

18-Jan-06 13:00:00 175.1887665 6885.88379 62.1169014 5.2262702

18-Jan-06 13:01:00 176.2958374 6894.43945 61.4315948 5.22509813

18-Jan-06 13:02:00 175.9198608 6902.99561 61.2291222 5.22392559

18-Jan-06 13:03:00 175.5081482 6918.58154 61.0266495 5.22275352

18-Jan-06 13:04:00 174.6976624 6876.62354 61.2686882 5.22158098

18-Jan-06 13:05:00 174.0641937 6859.02637 61.4048843 5.22040892

18-Jan-06 13:06:00 174.2192535 6860.49316 62.1219521 5.21923637

18-Jan-06 13:07:00 174.2867889 6883.01074 62.2532578 5.21806431

18-Jan-06 13:08:00 173.8604431 6953.37354 61.4449768 5.21689224

18-Jan-06 13:09:00 174.4386139 6908.13721 61.4348755 5.2157197

18-Jan-06 13:10:00 175.1759338 6888.18018 61.0292931 5.21454763

18-Jan-06 13:11:00 175.5333099 6896.15576 60.6237144 5.21337509

18-Jan-06 13:12:00 176.4559784 6911.73975 60.3050003 5.21220303

18-Jan-06 13:13:00 175.4448395 6920.64746 60.6061172 5.21103048

18-Jan-06 13:14:00 175.9410095 6925.13916 61.1296959 5.2172637

18-Jan-06 13:15:00 174.9229431 6918.58154 59.9890366 5.23141336

18-Jan-06 13:16:00 173.516449 6920.6416 61.4957123 5.24556303

18-Jan-06 13:17:00 174.9537659 7014.56348 61.8088303 5.25971222

18-Jan-06 13:18:00 174.6124878 7201.06445 62.1014214 5.27386189

18-Jan-06 13:19:00 175.4069824 7122.57031 61.2370605 5.28801107

18-Jan-06 13:20:00 174.986145 7101.40186 61.1912918 5.30216074

18-Jan-06 13:21:00 174.4548187 7052.47852 60.5958519 5.31631041

Page 2 of 6
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

18-Jan-06 13:22:00 175.5783691 7030.99365 60.7488403 5.33045959

18-Jan-06 13:23:00 176.3546906 7031.20703 60.9530487 5.34460926

18-Jan-06 13:24:00 175.3148499 6993.71436 61.1572571 5.35875893

18-Jan-06 13:25:00 174.5687408 6939.86768 61.0619011 5.35426903

18-Jan-06 13:26:00 174.5309143 6891.55566 60.9066353 5.32985401

18-Jan-06 13:27:00 173.8821869 6897.58203 60.3832397 5.30543947

18-Jan-06 13:28:00 175.297287 6962.73584 60.4127693 5.28102446

18-Jan-06 13:29:00 175.7769623 6901.83057 60.6180916 5.25660992

18-Jan-06 13:30:00 175.2662659 6859.58008 60.8234177 5.2321949

18-Jan-06 13:31:00 175.6753693 6859.58301 61.3310356 5.20778036

18-Jan-06 13:32:00 176.1211395 6844.54883 61.3868141 5.18336535

18-Jan-06 13:33:00 175.4292145 6844.53076 61.2383156 5.16211128

18-Jan-06 13:34:00 175.4152527 6862.86475 61.3993111 5.14423609

18-Jan-06 13:35:00 174.8561096 6859.63965 61.0063934 5.12636137

18-Jan-06 13:36:00 175.1764526 6894.03711 60.7601089 5.10848618

18-Jan-06 13:37:00 174.9116974 6906.49023 60.686676 5.09061098

18-Jan-06 13:38:00 174.2566986 6967.71191 60.3761444 5.07273579

18-Jan-06 13:39:00 175.1230011 6898.39209 60.7395782 5.05486059

18-Jan-06 13:40:00 174.8597717 6883.08691 60.7087784 5.07561827

18-Jan-06 13:41:00 175.271759 6884.18701 60.8091583 5.13767242

18-Jan-06 13:42:00 175.436554 6894.16064 61.266861 5.19972658

18-Jan-06 13:43:00 175.3068848 6901.31104 61.3459969 5.2308054

18-Jan-06 13:44:00 175.3873291 6900.21094 60.7810707 5.22877216

18-Jan-06 13:45:00 175.4045258 6881.05273 60.0774078 5.22673893

18-Jan-06 13:46:00 175.0319214 6859.91357 60.3853912 5.2247057

18-Jan-06 13:47:00 175.7885284 6868.30371 60.4345856 5.22267246

18-Jan-06 13:48:00 174.8809814 6953.22119 60.7405052 5.22063923

18-Jan-06 13:49:00 174.5594635 6862.74219 61.1982079 5.218606

18-Jan-06 13:50:00 174.7138672 6824.77246 61.4957123 5.21657276

18-Jan-06 13:51:00 173.7687531 6810.70313 61.1912918 5.21453953

18-Jan-06 13:52:00 174.1109619 6801.35889 61.003418 5.21250629

18-Jan-06 13:53:00 175.2093048 6803.27881 60.2519302 5.21047306

18-Jan-06 13:54:00 175.757019 6825.98584 60.4161911 5.20843983

18-Jan-06 13:55:00 174.5747375 6814.43555 60.7241783 5.20640659

18-Jan-06 13:56:00 175.1606903 6808.15576 60.2519302 5.20437336

18-Jan-06 13:57:00 175.3241272 6862.99951 60.3751259 5.20234013

18-Jan-06 13:58:00 175.1110229 6898.72119 60.87817 5.20030689

18-Jan-06 13:59:00 175.7521973 6861.31201 60.7771645 5.19827366

Page 3 of 6
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

18-Jan-06 14:00:00 176.2698822 6853.44189 60.3066025 5.19624043

18-Jan-06 14:01:00 175.3783264 6816.29932 60.7166405 5.19420719

18-Jan-06 14:02:00 175.438858 6842.81445 61.1266785 5.19217396

18-Jan-06 14:03:00 175.412796 6863.17871 61.7590294 5.19014072

18-Jan-06 14:04:00 173.9171906 6838.06494 61.1912918 5.18810749

18-Jan-06 14:05:00 174.4637909 6821.93799 61.1707611 5.18607426

18-Jan-06 14:06:00 173.9533691 6837.03223 60.565052 5.18404102

18-Jan-06 14:07:00 174.5837402 6842.79004 60.565052 5.18200779

18-Jan-06 14:08:00 174.5332642 6917.73145 61.1912918 5.17997456

18-Jan-06 14:09:00 175.1998901 6879.82373 60.2822304 5.17794132

18-Jan-06 14:10:00 174.7399902 6830.81104 59.9798775 5.17590809

18-Jan-06 14:11:00 174.2283325 6810.45605 60.2780228 5.17387486

18-Jan-06 14:12:00 174.4084473 6824.01221 60.5297012 5.17184162

18-Jan-06 14:13:00 174.5885468 6812.15137 60.0209427 5.16980839

18-Jan-06 14:14:00 175.7016144 6822.25928 60.2057343 5.16777515

18-Jan-06 14:15:00 174.6792145 6839.60498 59.9943657 5.16574192

18-Jan-06 14:16:00 174.2049103 6841.07129 60.4418564 5.16370821

18-Jan-06 14:17:00 175.961792 6863.30615 60.565052 5.16167498

18-Jan-06 14:18:00 175.2738342 6901.93457 59.7694168 5.15964174

18-Jan-06 14:19:00 175.0521851 6832.95557 60.3249931 5.15760851

18-Jan-06 14:20:00 174.6299896 6813.375 60.6276741 5.15557528

18-Jan-06 14:21:00 175.2909851 6819.6084 60.6559563 5.15354204

18-Jan-06 14:22:00 174.6742859 6818.11719 60.7824249 5.15150881

18-Jan-06 14:23:00 175.2992249 6807.11719 61.0929565 5.14947557

18-Jan-06 14:24:00 173.831543 6824.60254 60.474144 5.14744234

18-Jan-06 14:25:00 175.4128571 6809.44678 60.6485481 5.14540911

18-Jan-06 14:26:00 174.9641418 6837.18506 60.3751259 5.14337587

18-Jan-06 14:27:00 175.0481262 6822.14893 60.3751259 5.14134264

18-Jan-06 14:28:00 175.4333191 6890.60938 60.5804482 5.13930941

18-Jan-06 14:29:00 175.1222229 6828.59082 60.7857742 5.13727617

18-Jan-06 14:30:00 175.3648224 6794.93262 61.0296822 5.13524294

18-Jan-06 14:31:00 175.3373566 6804.83789 61.037384 5.13320971

18-Jan-06 14:32:00 174.9371338 6818.58789 60.7241783 5.13117647

18-Jan-06 14:33:00 174.3901672 6809.15771 60.7610817 5.12914324

18-Jan-06 14:34:00 173.9251251 6808.71094 61.1666603 5.13583994

18-Jan-06 14:35:00 174.8866425 6899.22314 61.5722427 5.15320683

18-Jan-06 14:36:00 175.2444458 6964.99121 61.5557404 5.17057323

18-Jan-06 14:37:00 175.4438934 7024.43945 61.6137733 5.18793964

Page 4 of 6
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

18-Jan-06 14:38:00 175.605484 7143.08643 61.6983757 5.20530653

18-Jan-06 14:39:00 175.4182587 7064.03662 61.3971367 5.22267294

18-Jan-06 14:40:00 174.2301331 6987.88672 61.287693 5.24003983

18-Jan-06 14:41:00 174.9073181 6952.13281 61.2811203 5.25740623

18-Jan-06 14:42:00 174.6211243 6926.32129 61.4311371 5.27477264

18-Jan-06 14:43:00 174.973175 6889.32568 61.2032204 5.29213953

18-Jan-06 14:44:00 174.1297607 6861.96338 60.9753036 5.29263878

18-Jan-06 14:45:00 175.0538635 6838.00391 60.7473869 5.27108145

18-Jan-06 14:46:00 175.5715485 6831.56836 60.7451782 5.24952412

18-Jan-06 14:47:00 176.1710663 6851.69922 61.4957123 5.22796679

18-Jan-06 14:48:00 175.2494507 6849.84717 61.1676369 5.20640945

18-Jan-06 14:49:00 173.8426056 6815.41602 59.8226547 5.18485212

18-Jan-06 14:50:00 176.5494843 6785.58691 60.5462303 5.16329479

18-Jan-06 14:51:00 175.2519684 6775.78418 60.4435692 5.14173746

18-Jan-06 14:52:00 175.2423401 6801.05762 60.3409042 5.12018013

18-Jan-06 14:53:00 175.5831909 6817.6416 60.3130264 5.0986228

18-Jan-06 14:54:00 173.6451263 6816.13086 60.7712517 5.07706547

18-Jan-06 14:55:00 175.9755707 6823.05518 61.1912918 5.05550766

18-Jan-06 14:56:00 175.3553467 6812.28125 61.1681938 5.04501724

18-Jan-06 14:57:00 175.9206085 6808.85254 60.7062111 5.05112648

18-Jan-06 14:58:00 174.4755402 6855.2373 60.2493439 5.05723572

18-Jan-06 14:59:00 174.1139679 6806.80127 60.0940781 5.06334543

18-Jan-06 15:00:00 175.1674042 6815.78271 59.9388123 5.06945467

18-Jan-06 15:01:00 176.3419952 6837.67041 60.5195999 5.07556391

18-Jan-06 15:02:00 176.635788 6855.08789 60.2700462 5.08167315

18-Jan-06 15:03:00 176.0706635 6844.20654 59.9595146 5.08778286

18-Jan-06 15:04:00 175.615097 6839.52441 60.5297012 5.0938921

18-Jan-06 15:05:00 174.4847717 6821.48096 60.0209427 5.10000134

18-Jan-06 15:06:00 174.0480042 6790.02979 59.9388123 5.10611057

18-Jan-06 15:07:00 174.2149048 6787.73779 59.9388123 5.11222029

18-Jan-06 15:08:00 174.0336609 6861.51123 59.8823471 5.11832952

18-Jan-06 15:09:00 174.0786896 6828.96484 60.1266823 5.12443876

18-Jan-06 15:10:00 173.9870911 6799.31396 60.2519302 5.130548

18-Jan-06 15:11:00 175.1311798 6798.36816 60.2519302 5.13665771

18-Jan-06 15:12:00 175.4116211 6835.25439 60.1058083 5.14276695

18-Jan-06 15:13:00 175.4289703 6821.3125 60.3832397 5.14887619

18-Jan-06 15:14:00 176.2326508 6838.43115 60.4572563 5.15315056

18-Jan-06 15:15:00 176.0241394 6825.52441 60.3032608 5.1548562

Page 5 of 6
Plant Information Database Query Results

Tag Name: 1pwrji900 1TSYFI100 1tmsti922m 1tsyai202

Tag Explanation: Unit Load Fuel Flow Inlet Temp Satuator

Tag Units: Mwe KCFH oF % H2O

18-Jan-06 15:16:00 175.4838715 6827.12549 59.8344383 5.15656137

18-Jan-06 15:17:00 174.9718018 6833.82715 60.2221107 5.15826702

18-Jan-06 15:18:00 174.7871857 6882.62842 60.565052 5.15997219

18-Jan-06 15:19:00 174.1124725 6830.92676 60.565052 5.16167784

18-Jan-06 15:20:00 173.6935272 6798.06055 60.0737305 5.16338348

18-Jan-06 15:21:00 173.905426 6816.99121 59.7682495 5.16508865

18-Jan-06 15:22:00 174.6641083 6835.92188 59.9596863 5.1667943

18-Jan-06 15:23:00 174.8918152 6854.85303 59.9706383 5.16849947

18-Jan-06 15:24:00 174.6805573 6873.78369 60.0322342 5.17020512

18-Jan-06 15:25:00 175.3742981 6880.52393 60.0938301 5.17191029

18-Jan-06 15:26:00 174.9732971 6870.28369 60.1554298 5.17361593

18-Jan-06 15:27:00 175.5291595 6926.63574 60.2170258 5.1753211

18-Jan-06 15:28:00 175.8404846 6990.96436 60.522274 5.17702675

18-Jan-06 15:29:00 175.6604614 6961.10986 60.4196129 5.1787324

18-Jan-06 15:30:00 175.4427185 6907.90088 60.3169518 5.18043756

18-Jan-06 15:31:00 173.762619 6886.08203 60.4033585 5.18214321

18-Jan-06 15:32:00 174.7630157 6889.18164 59.9413757 5.18384838

18-Jan-06 15:33:00 176.0535278 6873.1499 59.7232208 5.18555403

18-Jan-06 15:34:00 174.8758698 6859.06934 59.8464165 5.1872592

18-Jan-06 15:35:00 174.6839294 6855.76904 59.8031235 5.18896484

18-Jan-06 15:36:00 175.3010712 6852.46924 60.2807045 5.19067049

18-Jan-06 15:37:00 175.8595276 6849.16895 60.3822556 5.19237566

18-Jan-06 15:38:00 175.6854248 6918.53467 60.4838104 5.19408131

18-Jan-06 15:39:00 175.511322 6876.35156 60.4418564 5.19578648

18-Jan-06 15:40:00 175.3281097 6844.71387 59.9669304 5.19749212

18-Jan-06 15:41:00 175.0933075 6836.00537 60.1202927 5.35535908

18-Jan-06 15:42:00 174.8895264 6815.56299 60.2736588 5.35535908

Page 6 of 6
APPENDIX C 

FUEL ANALYSIS 

:

Source: Unit 1

CALCULATION OF DENSITY AND HEATING VALUE @ 60°F and 30 in Hg

% volume Component Gross 

*

Volume

% Molecular Density 

*

x Gross Weight Heating Value Fract.

Component Volume Wt. (lb/ft3) Density weight % Btu/lb Fract. Btu (Btu/SCF) Btu

Hydrogen 35.1600 2.016 0.0053 0.00186 3.2429 61100 1981.42 325.0 114.27Oxygen 0.0000 32.000 0.0846 0.00000 0.0000 0 0.00 0.0 0Argon 1.0690 39.948 0.1065 0.00114 1.9812 0 0.00 0.0 0Nitrogen 2.9900 28.016 0.0744 0.00222 3.8713 0 0.00 0.0 0CO2 16.9100 44.010 0.1170 0.01978 34.4303 0 0.00 0.0 0CO 43.8300 28.010 0.0740 0.03243 56.4435 4347 2453.60 322.0 141.1326COS 0.0000 60.070 0.1602 0.00000 0.0000 0 0.00 0.0 0Methane 0.0417 16.041 0.0424 0.00002 0.0308 23879 7.35 1013.0 0.422421Ethane 0.000 30.067 0.0803 0.00000 0.0000 22320 0.00 1792.0 0Ethylene 0.000 28.051 0.0746 0.00000 0.0000 21644 0.00 1614.0 0Propane 0.000 44.092 0.1196 0.00000 0.0000 21661 0.00 2590.0 0propylene 0.000 42.077 0.1110 0.00000 0.0000 21041 0.00 2336.0 0Isobutane 0.000 58.118 0.1582 0.00000 0.0000 21257 0.00 3363.0 0n-butane 0.000 58.118 0.1582 0.00000 0.0000 21308 0.00 3370.0 0Isobutene 0.000 56.102 0.1480 0.00000 0.0000 20730 0.00 3068.0 0Isopentane 0.000 72.144 0.1904 0.00000 0.0000 21052 0.00 4008.0 0n-pentane 72.144 0.1904 0.00000 0.0000 21091 0.00 4016.0 0n-hexane 86.169 0.2274 0.00000 0.0000 20940 0.00 4762.0 0H2S 34.076 0.0911 0.00000 0.0000 7100 0.00 647.0 0

Total: 100.00 Average Density 0.05746 100.0000 Gross Heating Value

Specific Gravity 0.75115 Btu/lb 4442 Btu/SCF 255.83

Btu/lb 4141 Btu/SCF 238

*

 Density (lb/ft3) and Gross Heating Value (Btu/scf) data from Perry's Chemical Engineering Hanbook.

Net Heating Value (Lower Heating Value), Btu/lb, calculated as Gross Heating Value (Higher Heating Value) - 10.30 (%H2 x 8.94)

Net Heating Values

Coal Derived Gas and Heating Value Calculations

Customer: Tampa Electric Company Sample ID Polk GC

Facility: Polk Power Station Analysis Date: 1/18/2006
:

Polk Power Station

Source: Unit 1

CALCULATION OF F FACTORS 

Weight Percents

Component Mol. Wt. C Factor H Factor % volume Fract. Wt. Carbon Hydrogen Nitrogen Oxygen

Hydrogen 2.016 0 1 35.160 70.8826 3.2666112

Oxygen 32.000 0 0 0.000 0.0000 0

Argon 39.948 0 0 1.069 42.7044Nitrogen 28.016 0 0 2.990 83.7678 3.860427239

CO2 44.010 0.272273 0 16.910 744.2091 9.33808036 24.933741CO 28.010 0.42587 0 43.830 1227.6783 24.0945978 32.515005COS 60.070 0.1998 0 0.000 0.0000 0 0Methane 16.041 0.75 0.25 0.042 0.6689 0.02311995 0.0077066Ethane 30.067 0.8 0.2 0.000 0.0000 0 0Ethylene 28.051 0.85714 0.14286 0.000 0.0000 0 0Propane 44.092 0.81818 0.181818 0.000 0.0000 0 0Propene 42.077 0.85714 0.14286 0.000 0.0000 0 0Isobutane 58.118 0.82759 0.17247 0.000 0.0000 0 0n-butane 58.118 0.82759 0.17247 0.000 0.0000 0 0Isobutene 56.102 0.85714 0.14286 0.000 0.0000 0 0Isopentane 72.144 0.83333 0.16667 0.000 0.0000 0 0n-pentane 72.144 0.83333 0.16667 0.000 0.0000 0 0n-hexane 86.169 0.83721 0.16279 0.000 0.0000 0 0H2S 34.076 0 0.0586923 0.000 0.0000 0 0Totals 100.00070 2169.9111 33.4557981 3.27 3.860427239 57.448746

CALCULATED VALUES

O2 F Factor (dry), Fd 8378 DSCF of Exhaust/MM Btu of Fuel Burned @ 0% excess airO2 F Factor (wet), Fw 9801 SCF of Exhaust/MM Btu of Fuel Burned @ 0% excess airMoisture F Factor 1423 SCF of Water/MM Btu of Fuel Burned @ 0% excess air

Combust. Moisture 14.51 volume % water in flue gas @ 0% excess airCO2 F Factor, Fc 2417 DSCF of CO2/MM Btu of Fuel Burned @ 0% excess air

Carbon Dioxide 28.85 volume % CO2 in flue gas @ 0% O2

Predicted Fo Factor 0.72 EPA Method 3a Fo value

Coal Derived Gas and Heating Value Calculations

Customer: Tampa Electric Company Sample ID Polk GC

Facility: Analysis Date: 1/18/2006
APPENDIX D 

CEMS DATA 
Polk **1 Compliance CEM Data 

Record# DATE TIME SO211 NOX12 CO213 OXY14

1 01/18/2006 121300 26.69 13.4 8.3 11

2 01/18/2006 121400 24.95 14.1 8.3 11

3 01/18/2006 121500 24.46 14.9 8.4 11

4 01/18/2006 121600 24.54 14.9 8.3 11

5 01/18/2006 121700 24.52 14.9 8.3 11

6 01/18/2006 121800 24.1 15 8.3 11

7 01/18/2006 121900 23.84 15.2 8.3 11

8 01/18/2006 122000 23.92 15.3 8.3 11

9 01/18/2006 122100 24.37 15.4 8.3 11

10 01/18/2006 122200 25.35 15.5 8.3 11

11 01/18/2006 122300 27.85 15.1 8.3 11

12 01/18/2006 122400 28.6 15 8.3 11

13 01/18/2006 122500 28.73 15.8 8.4 11

14 01/18/2006 122600 25.06 10.8 3.5 11

15 01/18/2006 122700 2.13 0.4 0.1 11

16 01/18/2006 122800 12.17 9.3 6.4 11.1

17 01/18/2006 122900 25.18 16.2 8.2 11

18 01/18/2006 123000 21.96 16.1 8.2 11

19 01/18/2006 123100 20.11 15.8 8.2 11

20 01/18/2006 123200 21.29 15.6 8.3 11

21 01/18/2006 123300 22.66 15.6 8.3 11

22 01/18/2006 123400 23.18 15.3 8.3 11

23 01/18/2006 123500 24.31 15.9 8.3 11

24 01/18/2006 123600 25.34 16.3 8.3 11

25 01/18/2006 123700 25.53 16.4 8.3 11

26 01/18/2006 123800 25.41 16.2 8.3 11.1

27 01/18/2006 123900 25.35 16.2 8.3 11.1

28 01/18/2006 124000 24.81 16.4 8.3 11.1

29 01/18/2006 124100 23.13 16.4 8.3 11

30 01/18/2006 124200 21.38 16.3 8.4 11

31 01/18/2006 124300 20.15 15.6 8.3 11

32 01/18/2006 124400 18.33 14.9 8.3 11

33 01/18/2006 124500 17.45 15.3 8.3 11

34 01/18/2006 124600 17.28 15.5 8.3 11

35 01/18/2006 124700 17.78 15.6 8.3 11

36 01/18/2006 124800 18.31 15.6 8.4 11

37 01/18/2006 124900 18.78 15.3 8.4 11

38 01/18/2006 125000 19.49 15.1 8.4 11

39 01/18/2006 125100 20.57 14.8 8.4 11
Record# DATE TIME SO211 NOX12 CO213 OXY14

40 01/18/2006 125200 22.01 14.2 8.3 11

41 01/18/2006 125300 22.97 13.4 8.3 11

42 01/18/2006 125400 22.34 13.6 8.3 11

43 01/18/2006 125500 22.44 14.2 8.3 11

44 01/18/2006 125600 22.97 14.3 8.3 11

45 01/18/2006 125700 23.28 14.1 8.3 11

46 01/18/2006 125800 23.91 14.1 8.3 11

47 01/18/2006 125900 24.55 14.4 8.3 11

48 01/18/2006 130000 24.94 14.6 8.3 11

49 01/18/2006 130100 24.6 14.6 8.3 11

50 01/18/2006 130200 24.38 14.6 8.3 11

51 01/18/2006 130300 24.24 14.1 8.2 11

52 01/18/2006 130400 22.9 14.1 8.3 11

53 01/18/2006 130500 21.95 14.8 8.3 11

54 01/18/2006 130600 21.91 15.1 8.3 11

55 01/18/2006 130700 22.07 14.9 8.3 11

56 01/18/2006 130800 22.25 14.7 8.3 11

57 01/18/2006 130900 23.22 14.8 8.3 11

58 01/18/2006 131000 23.81 14.9 8.3 11

59 01/18/2006 131100 24.48 14.8 8.3 11

60 01/18/2006 131200 25.93 14.8 8.3 11

61 01/18/2006 131300 28.4 14.5 8.3 11

62 01/18/2006 131400 27.02 14.3 8.2 11

63 01/18/2006 131500 25.53 14.5 8.3 11

64 01/18/2006 131600 25.8 14.4 8.3 11

65 01/18/2006 131700 27.17 14.6 8.3 11

66 01/18/2006 131800 28.96 14.5 8.3 11

67 01/18/2006 131900 28.42 14.4 8.3 11

68 01/18/2006 132000 26.24 14.3 8.3 11

69 01/18/2006 132100 24.95 13.8 8.2 11

70 01/18/2006 132200 25.77 13.4 8.2 10.9

71 01/18/2006 132300 25.85 12.9 8.2 10.9

72 01/18/2006 132400 24.8 12.8 8.3 10.9

73 01/18/2006 132500 25.65 12.8 8.3 11

74 01/18/2006 132600 27.5 12.7 8.2 11

75 01/18/2006 132700 29.32 13 8.2 11

76 01/18/2006 132800 30.08 13.5 8.3 11

77 01/18/2006 132900 30.28 13.7 8.3 11

78 01/18/2006 133000 30.03 13.8 8.3 11

79 01/18/2006 133100 29.56 14 8.3 11
Record# DATE TIME SO211 NOX12 CO213 OXY14

80 01/18/2006 133200 29.23 14.5 8.3 11

81 01/18/2006 133300 29.25 14.5 8.3 11

82 01/18/2006 133400 28.09 14.6 8.3 11

83 01/18/2006 133500 27.37 15.3 8.3 11

84 01/18/2006 133600 28.05 15.7 8.3 11

85 01/18/2006 133700 27.59 15.7 8.3 11

86 01/18/2006 133800 26.29 15.4 8.3 11

87 01/18/2006 133900 23.73 15.7 8.3 11

88 01/18/2006 134000 21.28 15.7 8.3 11

89 01/18/2006 134100 20.6 15.3 8.3 11

90 01/18/2006 134200 20.91 15.4 8.3 11

91 01/18/2006 134300 21.48 14.9 8.3 11

92 01/18/2006 134400 21.36 14.5 8.2 11

93 01/18/2006 134500 21.33 15.1 8.3 11

94 01/18/2006 134600 21.64 15.3 8.3 11

95 01/18/2006 134700 21.96 15.5 8.3 11

96 01/18/2006 134800 22.44 15.3 8.3 11

97 01/18/2006 134900 22.33 15.2 8.3 11

98 01/18/2006 135000 22.12 15.3 8.3 11

99 01/18/2006 135100 22.11 15.2 8.3 11

100 01/18/2006 135200 23.89 15.3 8.3 11

101 01/18/2006 135300 27.29 14.9 8.3 11

102 01/18/2006 135400 28.03 14.7 8.3 11

103 01/18/2006 135500 28.85 15.4 8.3 11

104 01/18/2006 135600 31.11 15.8 8.3 11

105 01/18/2006 135700 32.79 15.8 8.3 11.1

106 01/18/2006 135800 34.27 16.2 8.3 11.1

107 01/18/2006 135900 35.84 16.4 8.3 11.1

108 01/18/2006 140000 36.62 16.3 8.3 11

109 01/18/2006 140100 36.37 16.1 8.3 11

110 01/18/2006 140200 35.12 16.2 8.3 11

111 01/18/2006 140300 35.36 16 8.3 11

112 01/18/2006 140400 33.33 15.3 8.3 11

113 01/18/2006 140500 32.12 15.9 8.3 11

114 01/18/2006 140600 31.51 16.1 8.3 11.1

115 01/18/2006 140700 30.88 16 8.3 11

116 01/18/2006 140800 29.81 15.9 8.4 11

117 01/18/2006 140900 30.11 15.7 8.3 11.1

118 01/18/2006 141000 30.64 15.7 8.3 11.1

119 01/18/2006 141100 30.49 15.7 8.3 11.1
Record# DATE TIME SO211 NOX12 CO213 OXY14

120 01/18/2006 141200 30.92 15.7 8.3 11.1

121 01/18/2006 141300 31.39 15.4 8.3 11

122 01/18/2006 141400 30.22 15 8.3 11

123 01/18/2006 141500 29.37 15.6 8.3 11.1

124 01/18/2006 141600 30.29 15.7 8.3 11.1

125 01/18/2006 141700 31.88 16.2 8.3 11.1

126 01/18/2006 141800 33.09 16.1 8.3 11.1

127 01/18/2006 141900 34.24 16.3 8.3 11.1

128 01/18/2006 142000 33.91 16.4 8.3 11.1

129 01/18/2006 142100 32.65 16.1 8.3 11.1

130 01/18/2006 142200 31.37 16.4 8.3 11

131 01/18/2006 142300 31.45 16 8.3 11

132 01/18/2006 142400 30.49 15.2 8.3 11.1

133 01/18/2006 142500 29.33 15.6 8.3 11.1

134 01/18/2006 142600 29.12 16.2 8.3 11.1

135 01/18/2006 142700 29.33 16.5 8.3 11.1

136 01/18/2006 142800 28.93 16.4 8.3 11.1

137 01/18/2006 142900 28.87 16.4 8.3 11.1

138 01/18/2006 143000 29.52 16.3 8.3 11.1

139 01/18/2006 143100 29.83 16.5 8.3 11.1

140 01/18/2006 143200 30.85 16.7 8.3 11

141 01/18/2006 143300 31.82 16.2 8.3 11

142 01/18/2006 143400 29.87 15.4 8.3 11.1

143 01/18/2006 143500 27.96 15.7 8.3 11.1

144 01/18/2006 143600 27.26 16.1 8.3 11.1

145 01/18/2006 143700 27.4 16.1 8.3 11

146 01/18/2006 143800 27.74 16.2 8.3 11.1

147 01/18/2006 143900 27.85 16 8.3 11.1

148 01/18/2006 144000 27.39 15.6 8.3 11

149 01/18/2006 144100 28.42 15.1 8.3 11

150 01/18/2006 144200 30.41 14.6 8.3 11

151 01/18/2006 144300 32.86 13.3 8.2 11

152 01/18/2006 144400 34.43 12.9 8.2 11

153 01/18/2006 144500 36.26 13.5 8.2 11

154 01/18/2006 144600 37.61 14 8.3 11

155 01/18/2006 144700 39.73 14.2 8.3 11

156 01/18/2006 144800 41.56 14.3 8.2 11.1

157 01/18/2006 144900 42.51 14.5 8.2 11.1

158 01/18/2006 145000 43.43 15.2 8.3 11.1

159 01/18/2006 145100 42.91 15.6 8.3 11.1
Record# DATE TIME SO211 NOX12 CO213 OXY14

160 01/18/2006 145200 42.9 16.2 8.3 11

161 01/18/2006 145300 43.59 16 8.3 11.1

162 01/18/2006 145400 40.95 15.3 8.2 11.1

163 01/18/2006 145500 36.24 16.2 8.3 11.1

164 01/18/2006 145600 32.58 16.5 8.3 11.1

165 01/18/2006 145700 29.83 16.2 8.3 11.1

166 01/18/2006 145800 29.05 16.2 8.2 11.1

167 01/18/2006 145900 28.29 16.3 8.3 11.1

168 01/18/2006 150000 28.43 16.3 8.3 11.1

169 01/18/2006 150100 28.22 16.5 8.3 11.1

170 01/18/2006 150200 28.41 16.4 8.3 11.1

171 01/18/2006 150300 29.45 16.2 8.3 11.1

172 01/18/2006 150400 28.49 15.4 8.2 11.1

173 01/18/2006 150500 27.46 16 8.2 11.1

174 01/18/2006 150600 27.76 16.4 8.3 11.1

175 01/18/2006 150700 26.92 16.6 8.3 11.1

176 01/18/2006 150800 27.48 16.5 8.3 11.1

177 01/18/2006 150900 27.66 16.4 8.3 11.1

178 01/18/2006 151000 28.42 16.2 8.3 11.1

179 01/18/2006 151100 28.74 16 8.3 11.1

180 01/18/2006 151200 29.52 16.1 8.2 11.1

181 01/18/2006 151300 30.44 16.2 8.3 11.1

182 01/18/2006 151400 29.32 15.6 8.2 11.1

183 01/18/2006 151500 28.01 16.1 8.3 11.1

184 01/18/2006 151600 27.93 16.4 8.3 11.1

185 01/18/2006 151700 27.75 16.6 8.3 11.1

186 01/18/2006 151800 27.69 16.8 8.3 11.1

187 01/18/2006 151900 27.78 17 8.3 11.1

188 01/18/2006 152000 27.96 16.8 8.3 11.1

189 01/18/2006 152100 27.75 16.7 8.3 11.1

190 01/18/2006 152200 28.49 16.6 8.3 11.1

191 01/18/2006 152300 29.31 16.1 8.3 11.1

192 01/18/2006 152400 28.47 15.3 8.3 11.1

193 01/18/2006 152500 26.5 15.9 8.3 11.1

194 01/18/2006 152600 26.83 16.3 8.3 11.1

195 01/18/2006 152700 27.76 16.4 8.3 11.1

196 01/18/2006 152800 27.82 16.3 8.3 11.1

197 01/18/2006 152900 27.71 16 8.3 11.1

198 01/18/2006 153000 27.74 15.7 8.3 11.1

199 01/18/2006 153100 28.09 15.4 8.3 11.1
Record# DATE TIME SO211 NOX12 CO213 OXY14

200 01/18/2006 153200 29.04 15 8.3 11

201 01/18/2006 153300 30.28 14.9 8.3 11

202 01/18/2006 153400 29.75 14.4 8.3 11

203 01/18/2006 153500 29.7 14.5 8.2 11.1

204 01/18/2006 153600 30.93 14.4 8.2 11.1

205 01/18/2006 153700 32.32 14.7 8.2 11.1

206 01/18/2006 153800 33.09 15.2 8.3 11.1

207 01/18/2006 153900 33.05 15.3 8.3 11.1

208 01/18/2006 154000 33.03 15.7 8.3 11.1

209 01/18/2006 154100 32.71 15.8 8.3 11.1

210 01/18/2006 154200 32.59 15.6 8.3 11.1

211 / /

212 / / AVE 27.666 15.222 8.221 11.038
APPENDIX E 

VISIBLE EMISSIONS DATA SHEET 

APPENDIX F 

TEST PARTICIPANTS 
TEST PARTICIPANTS

AIR SERVICES GROUP 

ENVIRONMENTAL SERVICES

Juan Ramirez Environmental Technician 

Jorge Varino Technician 

POLK POWER STATION

Michael Perkins Environmental Coordinator