# Notes from Site Visit at the AES Cayuga Generation Plant on May 21, 2007

EPA conducted a site visit at the AES Cayuga Generation Plant on Monday, May 21, 2007 to

learn about the operations at the plant and dete rmine where and how samples would be collected

if the plant was selected for sampling. Table 1, at the end of this memorandum, identifies the

site visit participants.

This memorandum summarizes the information colle cted during the site vi sit, a pre-site visit

phone call held on May 10, 2007, and a June 22, 2007 le tter from John Marabella (AES Cayuga).

Overview of the Plant

• 

# New York State Electric and Gas (NYSEG ) sold the Cayuga plant to AES in 1999

(the plant was formerly named Milliken Station).

• 

# The plant operates two units, each with a capacity of about 150 MW and tangentialfired boilers. Unit 1 came on line in 1955 and Unit 2 came on line in 1958.

• 

# Cayuga is a baseload plant and it typically operates at full capacity.

• 

# The plant plans to shut down Unit 1 for a couple of weeks in October. During that

shutdown, the plant expects to reduce the flow rate of th e FGD absorber blowdown to

half of the typical flow rate. The pl ant expects to maintain the chlorides

concentration in the FGD absorber betw een 20,000 and 25,000 ppm, rather than the

typical 15,000 to 17,000 ppm. There are no other planned outages for 2007.

• 

# The plant burns about 2,500 tons of Eastern Bituminous coal per day. The coal

originates from lower Pennsylva nia, West Virginia, and Ea stern Ohio. Units 1 and 2

burn the same coal (or mixture of coals). The sulfur content of the coal ranges from

1.8 to 3.5%, with an approximate average of 2.5%.

• 

# The plant operates an ESP on each unit.

• 

# The plant operates an SCR on Unit 1 year round.

• 

# The plant operates a dry fly ash handling syst em. Some of the fly ash is marketable.

• 

# The plant operates a wet bottom ash sluice system. Bottom ash is sluiced from the

boiler hoppers to hydrobins (i .e., “decanting system”) in a batch process. The

decanted water is transferred to a decant tank. Plant personnel estimated that about

700 gpm of the bottom ash sluice water is recycled and 300 gpm is makeup water

from the house service water system. The overall system flowrate is approximately

1,000 gpm. Plant personnel stat ed that the plant does not te st water that is used as

bottom ash sluice because the water quality does not matter. The plant transfers

wastewater from the bottom ash sluicing system (the plant refers to this as “leakage”)

to the Process Water Reclamation Facility (PWRF), which is discussed in the “Other

WWT” section.

• 

# The plant pulverizes coal on site and removes the pyrit es generated using a hydrovac

system, in which a vacuum is created with a venturi jet. Wastewater from this system

is transferred to the PWRF. The pyrites are transferred to the on-site ash landfill or to

the coal pile.

• 

# The plant pulls its intake water from Cayuga Lake and does not treat this water. The

intake water is pumped through strainers to prevent zebra mussels from entering the

system. The plant uses the Cayuga Lake intake water for process water, including

# - 2 - once-through cooling water, and does not add chemicals to control biofouling or

zebra mussels. The plant mechanically removes zebra mussels by backwashing.

FGD System

• 

# The plant operates a wet FGD scrubber with two absorber compartments: one

absorber for each generating unit. The scrubber came on line in 1995.

• 

# The FGD scrubber is a three-level spray towe r (all three levels are typically operated

at one time), in which limestone is used as the sorbent.

• 

# Forced oxidation is used in the scrubber system.

• 

# Formic acid is added to the scrubber, whic h increases SO2 removal efficiency from

about 95% to 98-99%.

• 

# The plant maintains 8 to 13% solids in the scrubber. The plant maintains the

chlorides concentration below 20,000 ppm; however the absorber material of

construction (rubber-lined tile) can withstand 40,000 ppm chlorides.

• 

# The plant controls the chlorides and solids level with a continuous blowdown stream

from each absorber compartment. The blowdown streams from the two absorber

compartments are combined and transfe rred to primary hydrocyclones. Plant

personnel explained that the primary (a nd secondary) hydrocyclones contain two

separate banks of hydrocyclones, which would allow the plant to keep the two

blowdown streams separate throughout the solids separation process. The plant

currently has no need to operate in that fashion, however, because the two generating

units are operated similarly (i.e., they burn the same type of coal and operate at

capacity) and gypsum is generated from each blowdown stream.

• 

# Underflow from the primary hydrocyclones is transferred to centrifuges, in which

gypsum is separated. The dried gypsum is sold.

• 

# Overflow from the primary hydrocyclones is transferred to a secondary feed tank.

Water from the secondary feed tank is tr ansferred to secondary hydrocyclones when

they are operating, which is typically 8 to 10 hours per day. When the secondary

hydrocyclones are not operating, water from th e secondary feed tank is transferred to

the filtrate sump.

• 

# Underflow from the secondary hydrocyclones is transferred to the filtrate sump, in

which an “absorber module” filters the fine gypsum particles. Wa ter from the filtrate

sump is continuously recycled back to the scrubber.

• 

# Overflow from the secondary hydrocyclones ty pically contains less than 1% solids.

This overflow is transferred to two cl arified water tanks, which are connected

together. These clarified water tank s are each 60,000 gallons and agitated.

• 

# From the clarified water tanks, water is recycled as limestone ball mill makeup. A

bleed stream from the clarified water ta nk is transferred continuously to the FGD

WWT system at a flow rate of approxim ately 30 gpm. The residence time in the

clarified water tanks is about 72 hours.

# - 3 - FGD WWT

• 

# Wastewater is transferred c ontinuously from the clarified water tanks to the first unit

of the FGD WWT system, the equalization tank.

• 

# Wastewater is transferre d continuously at approx imately 30 gpm from the

equalization tank to the pH el evation tank. In the pH elev ation tank, lime slurry is

added to raise the wastewater pH to about 10.7 and initiate metal hydroxide

precipitation.

• 

# Wastewater is transferred from the pH elevation tank to the “heavy metals

precipitation tank”, which is an outdated na me. Organosulfide is no longer added to

the heavy metals precipitation tank and wa stewater simply passes through the tank.

Organosulfide was only added to the hea vy metals precipitation tank for one year

during Infilco Degremont’s startup perfor mance guarantee testi ng of the FGD WWT

system. During the guarantee testing, the plan t sampled at the influent and effluent of

the FGD WWT system, analyzing for “all” meta ls (total metals). After the guarantee

testing, the plant found that organosulfide addition was not necessary to maintain an

acceptable wastewater turbidity level (or to meet their limits, which are discussed in

the following section).

• 

# Wastewater is transferred from the heavy metals precipitation tank to the coagulation

tank. The plant adds ferric chloride con tinuously to the coag ulation tank, and has

done so for about one year. Plant personne l did not know the exact addition rate, but

knew that the plant uses approximately 1.5 dr ums (55 gallon drums) of ferric chloride

per month. Prior to one year ago, the plant added ferric chloride intermittently to the

coagulation tank for a period of a few months. During that time, the plant

experimented with system variables to op timize the FGD system and maintain a low

enough wastewater turbidity to allow recycl e (less than 5 to 7 NTU). The plant

determined that increasing the absorber pH to approximately 10.7 decreased the

turbidity to the target level. Currently, plant personnel doubt whet her ferric chloride

addition is necessary to maintain an acceptabl e wastewater turbidity level, but plan to

continue adding ferric chloride beca use the system is operating smoothly.

• 

# Wastewater is transferred from the coa gulation tank to the Densadeg unit. The

Densadeg unit consists of three sections/com partments: a reactor section, a thickener

section, and a clarifier secti on. Wastewater enters the Densadeg unit at the bottom of

the reactor section where it is mixed with a polymer flocculant. The water flows

upward through this reactor sec tion and enters the thickener section. In the thickener

section, water is forced downward by a system of baffles and floc particles settle at

the bottom of the thickener section by gravity. The sludge at the bottom of the

thickener section continues to thicken and is pushed into a cent er well by a rotary

scraper. Water travels upward from the thickener section into a clarifier section

where particles settle out in lamella modules.

• 

# Wastewater from the clarifier section of th e Densadeg unit is either transferred to a

storage tank or transferred di rectly to the PWRF. This wastewater flow rate is

typically between 30 and 40 gpm (difference from lime slurry and polymer addition).

# - 4 - • 

# Sludge from the Densadeg unit is transfe rred to a sludge holding tank. Sludge can be

recycled from the sludge holding tank to th e reactor tanks as seed, but this is not

typically done. Sludge is transferred from the sludge hol ding tank to a filter press.

• 

# Wastewater from the filter press is recycled to the equalization tank.

• 

# Plant personnel estimate the total residen ce time for the FGD wastewater treatment

system is 16.7 hours.

Sampling Information

• 

# The FGD WWT system influent sample coul d be taken at a sample tap between the

clarified water tanks and the equalization tank. This point is effectively between two

equalization stages prior to FGD WWT. Figur es 1 and 2 present photos of the sample

tap at the exit of the clarified water tanks.

• 

# Alternatively, the FGD WWT system influent could be sampled off the top of the

equalization tank. Figure 3 presents a phot o of the top of th e equalization tank.

• 

# The FGD WWT system effluent could be sa mpled at the tap where the plant samples

for turbidity. “Blowdown” from the FGD WWT system occurs two times per day for

about three to four hours. Flow is co ntinuous during those two periods. Plant

personnel stated that operators manually begin the blowdown process and could

coordinate with EPA/ERG samplers. Fi gures 4 and 5 present photos of the FGD

WWT system effluent sample tap.

• 

# The plant operates flow meters at the potential sampling points for the FGD WWT

system influent and effluent.

• 

# The plant stated that there would be su fficient space for a sampling staging area.

EPA/ERG could either use the control room or office space.

• 

# Samplers could either use the main boiler lab or the FGD lab for preservation. There

may only be a small amount of sp ace available in the FGD lab.

• 

# The plant stated that a FedEx pickup occurs daily at the plant loading dock.

Other WWT

• 

# The plant operates a WWT system for co al pile runoff and maintenance cleaning

washwater (CPR WWT system). Coal pile runoff is collected in a settling pond.

Water flows by gravity from the settli ng pond to a 500,000 gallon, concrete collection

basin. Water from the collection basin is e ither transferred directly to the CPR WWT

system or to the maintenance cleaning washwater tank and then to the CPR WWT

system. A portion of the maintenance clean ing washwater is air heater washwater.

The plant generates about 200,000 gal of air heater washwater twice per year. The

plant is prepared to accept coal pile runoff and maintenance cleaning waste from

other facilities (by tanker tr uck) in emergency situations and treat this water in the

CPR WWT system. The first stage of th e CPR WWT system is a pH adjustment

reactor, in which lime slurry and air is added. Water is transferred from the pH

adjustment reactor to a floc tank, in which polymer is added. The pH of the influent

to the pH adjustment reactor varies, but is typically around 7. The pH is typically

about 8.6 in the floc tank. Sludge from th e floc tank is transferred to the FGD WWT

# - 5 - system filter press. The filter press is used on an alternating basis for the FGD

wastewater and the coal pile runoff.

• 

# Process water/wastewater streams from the plan t, including effluent from the coal pile

runoff and FGD WWT systems, are sent to the PWRF. The PWRF includes oil/water

separation (API separators), dewatering/ solids separation, alum addition, and sand

filtration.

• 

# Wastewater from the PWRF (Outfall 001B) is combined with once-through

condenser cooling water. This combined st ream is then combined with wastewater

from the sanitary waste treatment system and discharged throu gh the plant’s final

outfall, 001.

Monitoring

• 

# The plant does not have monitoring data that could be used to compare the

characteristics of the FGD WWT effluent w ith and without ferric chloride addition.

• 

# The plant only measures turb idity and pH at the effluent of the FGD WWT system.

At that point, the turbidity is typically 1 to 2 NTU (the plant does not have TSS data)

and the chlorides con centration is approximately 20,000 ppm.

• 

# The plant samples wastewater at the efflue nt of the PWRF, Outfall 001B (prior to

commingling with cooling water) for limited pol lutants. The wastewater is monitored

for oil and grease, aluminum, TSS, and chlorides.

• 

# Outfall 001B is sampled weekly. See attached spreadsheet for sampling data.

Plant Flow Diagram

• 

# The plant flow diagram is attached.

# Figure 1. Sampling Location for Influent to F G D WWT System

(exit fro m c l arified w a ter tanks)

Figure 2. Sampling Location (close-up) for In fluent to F G D WWT System

(exit fro m c l arified w a ter tanks)

- 6 -

# Figure 3. Alternative S a mpling Location for Influent to F G D WWT System

(top of equaliz ation tank)

Figure 4. Sampling Location for E ffluent from FGD WWT System

- 7 -

# - 8 - Figure 5. Sampling Location (close-up) for Effluent from FGD WWT SystemTable 1. List of AttendeesNameOrganization (Representing)TelephoneE-mailPete BatrownyAES(703) 682-1141pete.batrowny@aes.comDan HillAES(607) 533-7913ext. 215dan.hill@aes.comBrian BalchikonisAES(607) 729-6950ext. 4116brian.balchikonis@aes.comJamie ChampionAES(607) 533-7913jamie.champion@aes.comJohn MarabellaAES(607) 533-7913john.marabella@aes.comFred GilletteNew York State Department ofEnvironmental Conservation(NYSDEC) Region 7(315) 426-7505Not givenJohn WeidmanNYSDEC - Albany(518)402-8197jmweidma@gw.dec.state.ny.usDonna HillSouthern Company(205) 587-4846dbhill@southernco.comLindy JohnsonTVA(423) 751-3361lpjohnson@tva.govRon JordanEPA/Office of Water(202) 566-1003jordan.ronald@epa.govSarah HolmanERG(703) 633-1661sarah.holman@erg.com001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim1/2/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 325.3 246. mg/l 5 KEY:1/2/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.5 LT = LESS THAN1/2/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 5 G*= QC duplicate failed RPD limits1/2/06 MISXPWXX01 PWRF G PH PH8.2 SU GH= analyzed past hold time1/3/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.219 mg/l 0.1 GR = QC reference failed limits1/3/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.01 MR= result not supplied1/3/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 4 GN = QC spike failed limits1/9/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 325.3 107. mg/l 51/9/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 51/9/06 MISXPWXX01 PWRF G PH PH8.1 SU1/10/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.237 mg/l 0.11/10/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.011/10/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 41/16/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 325.3 164. mg/l 51/16/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 51/16/06 MISXPWXX01 PWRF G PH PH8.0 SU1/17/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.238 mg/l 0.11/17/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.003 mg/l 0.011/17/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 41/23/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 325.3 340. mg/l 51/23/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 51/23/06 MISXPWXX01 PWRF G PH PH8.0 SU1/24/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.272 mg/l 0.11/24/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 LT 0.002 mg/l 0.011/24/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 G* LT 4. mg/l 41/30/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 325.3 366. mg/l 51/30/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 51/30/06 MISXPWXX01 PWRF G PH PH8.1 SU1/31/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.307 mg/l 0.11/31/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 LT 0.002 mg/l 0.011/31/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 42/6/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 268. mg/l2/6/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.52/6/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 52/6/06 MISXPWXX01 PWRF G PH PH8.1 SU2/8/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.252 mg/l 0.12/8/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 LT 0.002 mg/l 0.012/8/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 10. mg/l 42/13/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 181. mg/l2/13/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 52/13/06 MISXPWXX01 PWRF G PH PH8.2 SU2/14/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.235 mg/l 0.12/14/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.002 mg/l 0.012/14/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 42/21/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 38.8 mg/l2/21/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 52/21/06 MISXPWXX01 PWRF G PH PH8.3 SU2/22/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.277 mg/l 0.12/22/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.003 mg/l 0.012/22/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 42/27/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 164. mg/l2/27/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 52/27/06 MISXPWXX01 PWRF G PH PH8.1 SU2/28/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.302 mg/l 0.12/28/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.012/28/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 4Page 1001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim3/6/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.281 mg/l 0.13/6/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.013/6/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 4.0 mg/l 43/6/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 155. mg/l3/6/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.53/6/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 53/6/06 MISXPWXX01 PWRF G PH PH8.1 SU3/13/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 382. mg/l3/13/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 53/13/06 MISXPWXX01 PWRF G PH PH8.2 SU3/14/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.323 mg/l 0.13/14/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.013/14/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 43/20/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 220. mg/l3/20/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 53/20/06 MISXPWXX01 PWRF G PH PH7.6 SU3/21/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.276 mg/l 0.13/21/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.003 mg/l 0.013/21/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 43/27/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 246. mg/l3/27/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 53/27/06 MISXPWXX01 PWRF G PH PH8.0 SU3/28/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.281 mg/l 0.13/28/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.003 mg/l 0.013/28/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 44/3/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 388 mg/l4/3/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.54/3/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 54/3/06 MISXPWXX01 PWRF G PH PH8.2 SU4/4/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.335 mg/l 0.14/4/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.002 mg/l 0.014/4/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 6.5 mg/l 44/10/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 329 mg/l4/10/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 54/10/06 MISXPWXX01 PWRF G PH PH7.9 SU4/11/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.273 mg/l 0.14/11/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.014/11/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 44/17/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 211 mg/l4/17/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 54/17/06 MISXPWXX01 PWRF G PH PH8.0 SU4/19/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.290 mg/l 0.14/19/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.014/19/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 44/24/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 265 mg/l4/24/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 54/24/06 MISXPWXX01 PWRF G PH PH8.1 SU4/25/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.261 mg/l 0.14/25/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.014/25/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 12. mg/l 45/1/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 246 mg/l5/1/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.55/1/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/1/06 MISXPWXX01 PWRF G PH PH8.2 SU5/2/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.255 mg/l 0.15/2/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.003 mg/l 0.01Page 2001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim5/2/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 45/8/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 49.0 mg/l5/8/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/8/06 MISXPWXX01 PWRF G PH PH8.3 SU5/9/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.295 mg/l 0.15/9/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.015/9/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 5.0 mg/l 45/15/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 229 mg/l5/15/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/15/06 MISXPWXX01 PWRF G PH PH8.2 SU5/16/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.280 mg/l 0.15/16/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.015/16/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 45/22/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 178 mg/l5/22/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/22/06 MISXPWXX01 PWRF G PH PH8.2 SU5/23/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.323 mg/l 0.15/23/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.015/23/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 45/30/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 185 mg/l5/30/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/30/06 MISXPWXX01 PWRF G PH PH8.2 SU5/31/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.154 mg/l 0.15/31/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.002 mg/l 0.015/31/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 46/5/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 209 mg/l6/5/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.56/5/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 56/5/06 MISXPWXX01 PWRF G PH PH8.2 SU6/6/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.240 mg/l 0.16/6/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.016/6/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 46/12/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.327 mg/l 0.16/12/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.002 mg/l 0.016/12/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 GH LT 4.0 mg/l 46/12/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 196 mg/l6/12/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 56/12/06 MISXPWXX01 PWRF G PH PH8.3 SU6/21/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.291 mg/l 0.16/21/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.016/21/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 46/21/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 187 mg/l6/21/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 5.8 mg/l 56/21/06 MISXPWXX01 PWRF G PH PH8.0 SU6/26/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 106 mg/l6/26/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5.0 mg/l 56/26/06 MISXPWXX01 PWRF G PH PH8.1 SU6/27/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.355 mg/l 0.16/27/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.016/27/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 47/3/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) 1312/EPA 325.3 CNTRT 210 mg/l 27/3/06 MISXPWXX01 PWRF G NH3- AMMONIA Lachat COM LT 0.1 mg/l 0.17/3/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 CNTRT LT 5 mg/l 57/3/06 MISXPWXX01 PWRF G PH PH8.3 SU7/5/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 CNTRT 0.23 mg/l 0.17/5/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 CNTRT LT 0.050 mg/l 0.050Page 3001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim7/5/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 CNTRT 28 mg/l 57/10/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 136 mg/l7/10/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 6.5 mg/l 57/10/06 MISXPWXX01 PWRF G PH PH8.2 SU7/11/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.241 mg/l 0.17/11/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 LT 0.002 mg/l 0.017/11/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 47/17/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 156 mg/l7/17/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 57/17/06 MISXPWXX01 PWRF G PH PH8.2 SU7/18/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.220 mg/l 0.17/18/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 LT 0.002 mg/l 0.017/18/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 6.0 mg/l 47/24/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 212 mg/l7/24/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 57/24/06 MISXPWXX01 PWRF G PH PH8.1 SU7/25/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.194 mg/l 0.17/25/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.017/25/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 48/1/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.209 mg/l 0.18/1/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.018/1/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 48/1/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 149 mg/l8/1/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.58/1/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/1/06 MISXPWXX01 PWRF G PH PH8.0 SU8/8/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.161 mg/l 0.18/8/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.018/8/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 48/8/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 149 mg/l8/8/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 GN LT 5 mg/l 58/8/06 MISXPWXX01 PWRF G PH PH8.1 SU8/14/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 133 mg/l8/14/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/14/06 MISXPWXX01 PWRF G PH PH8.0 SU8/15/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.173 mg/l 0.18/15/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.018/15/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 48/21/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 61.2 mg/l8/21/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/21/06 MISXPWXX01 PWRF G PH PH8.1 SU8/22/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.278 mg/l 0.18/22/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.018/22/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 5.5 mg/l 48/28/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 136 mg/l8/28/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/28/06 MISXPWXX01 PWRF G PH PH8.1 SU8/29/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.253 mg/l 0.18/29/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.003 mg/l 0.018/29/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 4.5 mg/l 49/5/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 110 mg/l9/5/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.59/5/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/5/06 MISXPWXX01 PWRF G PH PH8.3 SU9/6/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.256 mg/l 0.19/6/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.01Page 4001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim9/6/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 49/11/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 40.5 mg/l9/11/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/11/06 MISXPWXX01 PWRF G PH PH8.1 SU9/12/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.259 mg/l 0.19/12/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.019/12/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 49/18/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.228 mg/l 0.19/18/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.003 mg/l 0.019/18/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 49/19/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 42.0 mg/l9/19/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/19/06 MISXPWXX01 PWRF G PH PH8.3 SU9/25/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 71.5 mg/l9/25/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/25/06 MISXPWXX01 PWRF G PH PH8.1 SU9/26/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.208 mg/l 0.19/26/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.019/26/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 410/2/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 101 mg/l10/2/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.510/2/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/2/06 MISXPWXX01 PWRF G PH PH8.2 SU10/3/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.250 mg/l 0.110/3/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0110/3/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 410/10/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 161 mg/l10/10/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 510/10/06 MISXPWXX01 PWRF G PH PH8.2 SU10/11/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.256 mg/l 0.110/11/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.0110/11/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 410/16/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 45.1 mg/l10/16/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5. mg/l 510/16/06 MISXPWXX01 PWRF G PH PH8.2 SU10/17/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.224 mg/l 0.110/17/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.002 mg/l 0.0110/17/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 410/23/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 85.8 mg/l10/23/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/23/06 MISXPWXX01 PWRF G PH PH8.1 SU10/25/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.170 mg/l 0.110/25/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.0110/25/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 410/30/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 170 mg/l10/30/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/30/06 MISXPWXX01 PWRF G PH PH8.3 SU10/31/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.210 mg/l 0.110/31/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.009 mg/l 0.0110/31/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 411/6/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 172 mg/l11/6/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.511/6/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/6/06 MISXPWXX01 PWRF G PH PH8.1 SU11/7/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.239 mg/l 0.111/7/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.01Page 5001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim11/7/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 411/13/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 412 mg/l11/13/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/13/06 MISXPWXX01 PWRF G PH PH8.2 SU11/14/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.128 mg/l 0.111/14/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0111/14/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 411/20/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 53.6 mg/l11/20/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/20/06 MISXPWXX01 PWRF G PH PH8.1 SU11/22/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.167 mg/l 0.111/22/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.0111/22/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 411/27/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 280 mg/l11/27/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/27/06 MISXPWXX01 PWRF G PH PH8.1 SU11/28/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.076 mg/l 0.05011/28/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.01011/28/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 412/4/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 167 mg/l12/4/06 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.512/4/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 512/4/06 MISXPWXX01 PWRF G PH PH8.2 SU12/5/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.199 mg/l 0.05012/5/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.01012/5/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 412/11/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.221 mg/l 0.05012/11/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.01012/11/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 412/12/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 100 mg/l12/12/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 512/12/06 MISXPWXX01 PWRF G PH PH7.9 SU12/18/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 166 mg/l12/18/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 512/18/06 MISXPWXX01 PWRF G PH PH7.9 SU12/19/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.178 mg/l 0.05012/19/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.01012/19/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 412/26/06 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 280 mg/l12/26/06 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 512/26/06 MISXPWXX01 PWRF G PH PH8.0 SU12/27/06 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.116 mg/l 0.05012/27/06 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.01012/27/06 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 41/2/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 44.9 mg/l1/2/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.51/2/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 51/2/07 MISXPWXX01 PWRF G PH PH8.1 SU1/3/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.160 mg/l 0.0501/3/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.0101/3/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4.0 mg/l 41/8/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 157 mg/l1/8/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 51/8/07 MISXPWXX01 PWRF G PH PH7.9 SU1/9/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.161 mg/l 0.0501/9/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.010Page 6001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim1/9/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4. mg/l 41/15/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.244 mg/l 0.0501/15/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0101/15/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 41/16/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 51.5 mg/l1/16/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 GR LT 5 mg/l 51/16/07 MISXPWXX01 PWRF G PH PH8.0 SU1/22/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 258 mg/l1/22/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 GR LT 5 mg/l 51/22/07 MISXPWXX01 PWRF G PH PH8.0 SU1/23/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.069 mg/l 0.0501/23/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.0101/23/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 41/29/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 151 mg/l1/29/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 51/29/07 MISXPWXX01 PWRF G PH PH8.2 SU1/30/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.193 mg/l 0.0501/30/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0101/30/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 42/5/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 268 mg/l2/5/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.52/5/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 52/5/07 MISXPWXX01 PWRF G PH PH8.0 SU2/6/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.308 mg/l 0.0502/6/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0102/6/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 42/12/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 237 mg/l2/12/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 52/12/07 MISXPWXX01 PWRF G PH PH7.9 SU2/13/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.263 mg/l 0.0502/13/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.0102/13/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 42/19/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 73.8 mg/l2/19/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 52/19/07 MISXPWXX01 PWRF G PH PH8.0 SU2/20/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.249 mg/l 0.0502/20/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0102/20/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 42/26/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 82.6 mg/l2/26/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 52/26/07 MISXPWXX01 PWRF G PH PH7.9 SU2/27/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.384 mg/l 0.0502/27/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0102/27/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 43/5/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 239 mg/l3/5/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 53/5/07 MISXPWXX01 PWRF G PH PH8.1 SU3/6/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.174 mg/l 0.0503/6/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0103/6/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 43/6/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.53/12/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 231 mg/l3/12/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 53/12/07 MISXPWXX01 PWRF G PH PH7.9 SU3/13/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.473 mg/l 0.0503/13/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.010Page 7001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim3/13/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 43/19/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 235 mg/l3/19/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 53/19/07 MISXPWXX01 PWRF G PH PH8.0 SU3/20/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.261 mg/l 0.0503/20/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.0103/20/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 43/26/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.393 mg/l 0.0503/26/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.0103/26/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 8.5 mg/l 43/26/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 256 mg/l3/26/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 53/26/07 MISXPWXX01 PWRF G PH PH8.1 SU4/2/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 227 mg/l4/2/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.54/2/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 54/2/07 MISXPWXX01 PWRF G PH PH8.1 SU4/3/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.235 mg/l 0.0504/3/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.0104/3/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 44/9/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 268 mg/l4/9/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 54/9/07 MISXPWXX01 PWRF G PH PH8.1 SU4/10/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.250 mg/l 0.0504/10/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0104/10/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 6.0 mg/l 44/16/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 156 mg/l4/16/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 54/16/07 MISXPWXX01 PWRF G PH PH8.1 SU4/17/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.280 mg/l 0.0504/17/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.0104/17/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 4.5 mg/l 44/23/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 196 mg/l4/23/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 54/23/07 MISXPWXX01 PWRF G PH PH7.8 SU4/24/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.194 mg/l 0.0504/24/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0104/24/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 44/30/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 485 mg/l4/30/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 COM LT 0.50 mg/l 0.54/30/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 54/30/07 MISXPWXX01 PWRF G PH PH7.9 SU5/1/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.253 mg/l 0.0505/1/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0105/1/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 45/7/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 273 mg/l5/7/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/7/07 MISXPWXX01 PWRF G PH PH8.0 SU5/8/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.270 mg/l 0.0505/8/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.0105/8/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 45/14/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 170 mg/l5/14/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/14/07 MISXPWXX01 PWRF G PH PH8.3 SU5/15/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.274 mg/l 0.0505/15/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.010Page 8001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim5/15/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 45/21/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 87.0 mg/l5/21/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/21/07 MISXPWXX01 PWRF G PH PH8.3 SU5/22/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.351 mg/l 0.0505/22/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0105/22/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 45/29/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 89.6 mg/l5/29/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 55/29/07 MISXPWXX01 PWRF G PH PH8.2 SU5/30/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.194 mg/l 0.0505/30/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.0105/30/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 4.0 mg/l 46/4/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 192 mg/l6/4/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.56/4/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 56/4/07 MISXPWXX01 PWRF G PH PH8.0 SU6/5/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.170 mg/l 0.0506/5/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0106/5/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 46/11/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 98.2 mg/l6/11/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 56/11/07 MISXPWXX01 PWRF G PH PH8.0 SU6/12/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.161 mg/l 0.0506/12/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0106/12/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 46/18/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 59.8 mg/l6/18/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 56/18/07 MISXPWXX01 PWRF G PH PH8.2 SU6/19/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.217 mg/l 0.0506/19/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0106/19/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 46/25/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 112 mg/l6/25/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 56/25/07 MISXPWXX01 PWRF G PH PH8.2 SU6/26/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.221 mg/l 0.0506/26/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0106/26/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 47/2/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 192 mg/l7/2/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.57/2/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 57/2/07 MISXPWXX01 PWRF G PH PH8.0 SU7/3/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.153 mg/l 0.0507/3/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0107/3/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 47/9/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 166 mg/l7/9/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 57/9/07 MISXPWXX01 PWRF G PH PH8.0 SU7/10/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.243 mg/l 0.0507/10/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.0017/10/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 47/16/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 56.4 mg/l7/16/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 57/16/07 MISXPWXX01 PWRF G PH PH8.0 SU7/17/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.334 mg/l 0.0507/17/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.010Page 9001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim7/17/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 47/23/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 116 mg/l7/23/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 57/23/07 MISXPWXX01 PWRF G PH PH8.1 SU7/24/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.286 mg/l 0.0507/24/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.005 mg/l 0.0107/24/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 4.0 mg/l 47/30/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 125 mg/l7/30/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 57/30/07 MISXPWXX01 PWRF G PH PH8.0 SU7/31/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.401 mg/l 0.0507/31/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0107/31/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 4.0 mg/l 48/6/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 51.4 mg/l8/6/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.58/6/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/6/07 MISXPWXX01 PWRF G PH PH7.8 SU8/7/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.370 mg/l 0.0508/7/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.0108/7/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 48/14/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.420 mg/l 0.0508/14/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0108/14/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 48/15/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 174 mg/l8/15/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/15/07 MISXPWXX01 PWRF G PH PH7.8 SU8/20/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 48.6 mg/l8/20/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/20/07 MISXPWXX01 PWRF G PH PH7.8 SU8/21/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.251 mg/l 0.0508/21/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0108/21/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 5.5 mg/l 48/27/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 126 mg/l8/27/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 58/27/07 MISXPWXX01 PWRF G PH PH8.0 SU8/28/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.162 mg/l 0.0508/28/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0108/28/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 49/4/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 121 mg/l9/4/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.59/4/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/4/07 MISXPWXX01 PWRF G PH PH7.9 SU9/5/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.207 mg/l 0.0509/5/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0109/5/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 49/10/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 45.8 mg/l9/10/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/10/07 MISXPWXX01 PWRF G PH PH8.0 SU9/11/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.442 mg/l 0.0509/11/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.0109/11/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 49/17/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 47.5 mg/l9/17/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/17/07 MISXPWXX01 PWRF G PH PH8.0 SU9/18/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.158 mg/l 0.0509/18/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.004 mg/l 0.010Page 10001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim9/18/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 49/24/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 57.6 mg/l9/24/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 59/24/07 MISXPWXX01 PWRF G PH PH7.8 SU9/25/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.179 mg/l 0.0509/25/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.0109/25/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 410/1/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 51.7 mg/l10/1/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.510/1/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/1/07 MISXPWXX01 PWRF G PH PH7.7 SU10/2/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.375 mg/l 0.02010/2/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.01010/2/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 410/8/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 144 mg/l10/8/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/8/07 MISXPWXX01 PWRF G PH PH8.1 SU10/10/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.172 mg/l 0.02010/10/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.01010/10/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 4.0 mg/l 410/15/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 43.9 mg/l10/15/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/15/07 MISXPWXX01 PWRF G PH PH8.0 SU10/16/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.163 mg/l 0.02010/16/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.01010/16/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 410/22/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 43.5 mg/l10/22/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/22/07 MISXPWXX01 PWRF G PH PH EPA 150.1 8.1 SU10/23/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.124 mg/l 0.02010/23/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.01010/23/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 410/30/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.140 mg/l 0.02010/30/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.008 mg/l 0.01010/30/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 410/30/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 41.7 mg/l10/30/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 510/30/07 MISXPWXX01 PWRF G PH PH EPA 150.1 8.0 SU11/5/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 43.0 mg/l11/5/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 MR mg/l 0.511/5/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/5/07 MISXPWXX01 PWRF G PH PH EPA 150.1 8.3 SU11/6/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.136 mg/l 0.02011/6/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.011 mg/l 0.01011/6/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 411/12/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 73.3 mg/l11/12/07 MISXPWXX01 PWRF G NH3- AMMONIA EPA 350.3 LT 0.50 mg/l 0.511/12/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/12/07 MISXPWXX01 PWRF G PH PH EPA 150.1 8.2 SU11/13/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.162 mg/l 0.02011/13/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.009 mg/l 0.01011/13/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 411/19/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 108 mg/l11/19/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/19/07 MISXPWXX01 PWRF G PH PH EPA 150.1 8.0 SU11/20/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.134 mg/l 0.020Page 11001B outfall analysis dataCollection Date Sample Id Description Sample Type Substance Name Analysis Method ErrorCode Notation Concentration Units DetLim11/20/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.007 mg/l 0.01011/20/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 LT 4 mg/l 411/26/07 MISXPWXX01 PWRF G CL2- CHLORIDE (non-potable) EPA 300.0 98.7 mg/l11/26/07 MISXPWXX01 PWRF G O-G- OIL AND GREASE EPA 1664 LT 5 mg/l 511/26/07 MISXPWXX01 PWRF G PH PH EPA 150.1 8.1 SU11/27/07 MISXPWXX01 PWRF C24 AL-T ALUMINUM, TOTAL 40CFR 200.7 0.214 mg/l 0.02011/27/07 MISXPWXX01 PWRF C24 CU-T COPPER, TOTAL 40CFR 200.7 0.006 mg/l 0.01011/27/07 MISXPWXX01 PWRF C24 TSS- TOTAL SUSPENDED SOLIDS EPA 160.2 5.0 mg/l 412/3/07 MISXPWXX01 PWRF G PH PH EPA 150.1 8.1 SUPage 12