### 13339 Hagers Ferry Road Huntersville, NC 28078-7929 McGuire Nuclear Complex - MG03A2 Phone: 980-875-5245 Fax: 980-875-4349



# Order Summary Report 

# Analytical Laboratory

Order Number: J12080361 Project Name: Somerville Waste Water

Lab Contact: Jason C Perkins 

### Date: 9/14/2012 Customer Address: 253 Plant Allen Road Customer Name(s): BillK-RonL--RobnJ-DonS

Belmont, NC 28012

Phone: 980-875-5348 Report Authorized By: (Signature)


### Program Comments: Please contact the Program Manager (Jason C Perk ins) with any questions regarding this report. Data Flags & Calculations: Any analytical tests or individual analytes within a test flagged with a Qualifier indicate a deviation from the method quality system or quality control requirement. The qualifier description is found at the end of the Certificate of Analysis (sample re sults) under the qualifiers heading. All results are reported on a dry weight basis unless otherwise noted. Subcontracted data included on the Duke Certificate of Analysis is to be used as information only. Certified vendor results can be found in the subcontracted lab final report. Duke Energy Analytical Laboratory subcontracts analyses to other vendor laboratories that have been qualified by Duke Energy to perform these analyses except where noted. Data Package: This data package includes analytical results that are applicable only to the samples described in this narrative. An estimatio n of the uncertainty of measurement for the results in the report is available upon request. This report shall not be reproduced, except in full, without the written consent of the Analytical Laboratory. Please contact the Analytical laboratory with any questions. The order of individual sections within this report is as follows: Job Summary Report, Sample Identification, Technical Validation of Data Package, Analytical Laboratory Certificate of Analysis, Analytical Laboratory QC Reports, Sub-contracted Laboratory Results, Customer Specific Data Sheets, Reports & Documentation, Customer Database Entries, Test Case Narratives, Chain of Custody (COC) Certification: The Analytical Laboratory holds the following State Certificati ons : North Carolina (DENR) Certificate #248, South Carolina (DHEC) Laboratory ID # 99005. Contact t he Analytical Laboratory for definitive inform ation about the certification status of specific methods.

## Sample ID's & Descriptions:
Sample ID Plant/Station Collection Date and Time Collected By Sample Description 2012018261 ALLEN 20-Aug-12 8:15 AM Jeff Womack FGD Purge Eff 2012018262 ALLEN 20-Aug-12 8:15 AM BILL HASKINS EQ Tank Eff 2012018263 ALLEN 20-A ug-12 8:19 AM BI LL HASKINS Bi oReactor 1 Inf 2012018264 ALLEN 20-Aug-12 8:40 AM JEFF/BILL BioReactor 1 Inf BLANK 2012018265 ALLEN 20-A ug-12 8:30 AM BI LL HASKINS Bi oReactor 2 Inf 2012018266 ALLEN 20-Aug-12 8:50 AM JEFF/BILL BioReactor 2 Inf BLANK 2012018267 ALLEN 20-A ug-12 8:24 AM BI LL HASKINS Bi oReactor 2 Eff 2012018268 ALLEN 20-Aug-12 8:45 AM JEFF/BILL BioReactor 2 Eff BLANK 2012018269 ALLEN 20-A ug-12 11:30 AM BILL HASKINS Filter Blk 9 Total Samples

### COC and .pdf report are in agreement with sample totals and analyses (compliance programs and procedures). All Results are less than the laboratory reporting limits. All laboratory QA/QC requirements are acceptable. Yes No 

# Technical Validation Review Checklist:

Yes No

Yes No



## Report Sections Included: Job Summary Report Sub-contracted Laboratory Results Sample Identification Customer Specific Data Sheets, Reports, & Documentation Technical Validation of Data Package Customer Database Entries Analytical Laboratory Certificate of Analysis Analytical Laboratory QC Report Chain of Custody

Reviewed By: 

### Mary Ann Ogle Date: 

### 9/14/2012 Electronic Data Deliverable (EDD) Sent Separately

# Certificate of Laboratory Analysis This report shall not be re produced, exce pt in full. 

## Order # J12080361

2012018261 Collection Date: 20-Aug-12 8:15 AM 

### Site: FGD Purge Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF ALKALINITY - (Analysis Performed by Prism Labs) Vendor Parameter Complete Vendor Method V_PRISM INORGANIC IONS BY IC Bromide 6.0 mg/L EPA 300.0 8/27/2012 6:59:00 PM JAHERMA 5 50 Chloride 1300 mg/L EPA 300.0 8/27/2012 6:59:00 PM JAHERMA 50 500 Sulfate 1700 mg/L EPA 300.0 8/27/2012 6:59:00 PM JAHERMA 50 500 MERCURY (COLD VAPOR) IN WATER Mercury (Hg) 44.4 ug/L EPA 245.1 8/23/2012 1:39:27 PM AGIBBS 2.5 50 DISSOLVED METALS BY ICP Manganese (Mn) < 0.05 mg/L EPA 200.7 8/24/2012 10:54:00 AM DJSULL1 0.05 10 TOTAL RECOVERABLE METALS BY ICP Boron (B) 120 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 0.5 10 Calcium (Ca) 1370 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 0.1 10 Iron (Fe) 76.5 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 0.1 10 Lithium (Li) 0.118 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 0.05 10 Magnesium (Mg) 483 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 0.05 10 Manganese (Mn) 1.98 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 0.05 10 Potassium (K) 29.7 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 1 10 Sodium (Na) 24.5 mg/L EPA 200.7 8/28/2012 12:07:00 PM MHH7131 0.5 10 DISSOLVED METALS BY ICP-MS Selenium (Se) 748 ug/L EPA 200.8 8/24/2012 2:21:00 PM KRICHAR 10 10 TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) 119 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 Cadmium (Cd) < 10 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 Chromium (Cr) 149 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 Copper (Cu) 117 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 Nickel (Ni) 155 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 Selenium (Se) 748 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 Silver (Ag) < 10 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 Zinc (Zn) 232 ug/L EPA 200.8 8/29/2012 1:19:00 PM KRICHAR 10 10 SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC) Vendor Parameter Complete Vendor Method V_AS&C TOTAL DISSOLVED SOLIDS TDS 7900 mg/L SM2540C 8/22/2012 4:00:00 PM TJA7067 200 1 TOTAL SUSPENDED SOLIDS TSS 2200 mg/L SM2540D 8/23/2012 10:08:00 AM TJA7067 250 1

# Certificate of Laboratory Analysis This report shall not be re produced, exce pt in full. 

## Order # J12080361

2012018261 Collection Date: 20-Aug-12 8:15 AM 

### Site: FGD Purge Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF


### 2012018262 Collection Date: 20-Aug-12 8:15 AM 

### Site: EQ Tank Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF MERCURY (COLD VAPOR) IN WATER Mercury (Hg) 26.5 ug/L EPA 245.1 8/23/2012 1:41:47 PM AGIBBS 2.5 50 DISSOLVED METALS BY ICP Manganese (Mn) < 0.05 mg/L EPA 200.7 8/24/2012 10:57:00 AM DJSULL1 0.05 10 TOTAL RECOVERABLE METALS BY ICP Boron (B) 131 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 0.5 10 Calcium (Ca) 1220 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 0.1 10 Iron (Fe) 38.5 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 0.1 10 Lithium (Li) 0.085 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 0.05 10 Magnesium (Mg) 465 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 0.05 10 Manganese (Mn) 1.02 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 0.05 10 Potassium (K) 23.7 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 1 10 Sodium (Na) 40.1 mg/L EPA 200.7 8/28/2012 12:11:00 PM MHH7131 0.5 10 DISSOLVED METALS BY ICP-MS Selenium (Se) 591 ug/L EPA 200.8 8/24/2012 2:25:00 PM KRICHAR 10 10 TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) 58.8 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10 Cadmium (Cd) < 10 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10 Chromium (Cr) 81.2 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10 Copper (Cu) 58.0 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10 Nickel (Ni) 80.5 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10 Selenium (Se) 568 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10 Silver (Ag) < 10 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10 Zinc (Zn) 109 ug/L EPA 200.8 8/29/2012 1:22:00 PM KRICHAR 10 10


### 2012018263 Collection Date: 20-Aug-12 8:19 AM 

### Site: BioReactor 1 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF ALKALINITY - (Analysis Performed by Prism Labs) Vendor Parameter Complete Vendor Method V_PRISM

# Certificate of Laboratory Analysis This report shall not be re produced, exce pt in full. 

## Order # J12080361

2012018263 Collection Date: 20-Aug-12 8:19 AM 

### Site: BioReactor 1 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND DISSOLVED METALS BY ICP Manganese (Mn) < 0.05 mg/L EPA 200.7 8/24/2012 11:01:00 AM DJSULL1 0.05 10 TOTAL RECOVERABLE METALS BY ICP Boron (B) 172 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 0.5 10 Calcium (Ca) 1470 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 0.1 10 Iron (Fe) < 0.1 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 0.1 10 Lithium (Li) 0.060 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 0.05 10 Magnesium (Mg) 555 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 0.05 10 Manganese (Mn) < 0.05 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 0.05 10 Potassium (K) 17.5 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 1 10 Sodium (Na) 73.0 mg/L EPA 200.7 8/28/2012 12:15:00 PM MHH7131 0.5 10 DISSOLVED METALS BY ICP-MS Selenium (Se) 844 ug/L EPA 200.8 8/24/2012 2:29:00 PM KRICHAR 10 10 TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) < 10 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 Cadmium (Cd) < 10 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 Chromium (Cr) 16.7 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 Copper (Cu) < 10 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 Nickel (Ni) < 10 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 Selenium (Se) 843 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 Silver (Ag) < 10 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 Zinc (Zn) < 10 ug/L EPA 200.8 8/29/2012 1:25:00 PM KRICHAR 10 10 SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC) Vendor Parameter Complete Vendor Method V_AS&C


### 2012018264 Collection Date: 20-Aug-12 8:40 AM 

### Site: BioReactor 1 Inf BLANK Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND

# Certificate of Laboratory Analysis This report shall not be re produced, exce pt in full. 

## Order # J12080361

2012018264 Collection Date: 20-Aug-12 8:40 AM 

### Site: BioReactor 1 Inf BLANK Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND


### 2012018265 Collection Date: 20-Aug-12 8:30 AM 

### Site: BioReactor 2 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF ALKALINITY - (Analysis Performed by Prism Labs) Vendor Parameter Complete Vendor Method V_PRISM MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND DISSOLVED METALS BY ICP Manganese (Mn) < 0.05 mg/L EPA 200.7 8/24/2012 11:05:00 AM DJSULL1 0.05 10 TOTAL RECOVERABLE METALS BY ICP Boron (B) 179 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 0.5 10 Calcium (Ca) 1510 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 0.1 10 Iron (Fe) 0.103 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 0.1 10 Lithium (Li) 0.063 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 0.05 10 Magnesium (Mg) 568 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 0.05 10 Manganese (Mn) < 0.05 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 0.05 10 Potassium (K) 29.4 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 1 10 Sodium (Na) 73.9 mg/L EPA 200.7 8/28/2012 12:19:00 PM MHH7131 0.5 10 DISSOLVED METALS BY ICP-MS Selenium (Se) 72.5 ug/L EPA 200.8 8/24/2012 2:33:00 PM KRICHAR 10 10 TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) < 10 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10 Cadmium (Cd) < 10 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10 Chromium (Cr) < 10 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10 Copper (Cu) < 10 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10 Nickel (Ni) < 10 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10 Selenium (Se) 86.8 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10 Silver (Ag) < 10 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10 Zinc (Zn) < 10 ug/L EPA 200.8 8/29/2012 1:28:00 PM KRICHAR 10 10

# Certificate of Laboratory Analysis This report shall not be re produced, exce pt in full. 

## Order # J12080361

2012018265 Collection Date: 20-Aug-12 8:30 AM 

### Site: BioReactor 2 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC) Vendor Parameter Complete Vendor Method V_AS&C


### 2012018266 Collection Date: 20-Aug-12 8:50 AM 

### Site: BioReactor 2 Inf BLANK Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND


### 2012018267 Collection Date: 20-Aug-12 8:24 AM 

### Site: BioReactor 2 Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF ALKALINITY - (Analysis Performed by Prism Labs) Vendor Parameter Complete Vendor Method V_PRISM INORGANIC IONS BY IC Bromide 11 mg/L EPA 300.0 8/27/2012 7:17:00 PM JAHERMA 5 50 Chloride 2600 mg/L EPA 300.0 8/27/2012 7:17:00 PM JAHERMA 50 500 Sulfate 1900 mg/L EPA 300.0 8/27/2012 7:17:00 PM JAHERMA 50 500 MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND DISSOLVED METALS BY ICP Manganese (Mn) < 0.05 mg/L EPA 200.7 8/24/2012 11:09:00 AM DJSULL1 0.05 10

# Certificate of Laboratory Analysis This report shall not be re produced, exce pt in full. 

## Order # J12080361

2012018267 Collection Date: 20-Aug-12 8:24 AM 

### Site: BioReactor 2 Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF TOTAL RECOVERABLE METALS BY ICP Boron (B) 188 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 0.5 10 Calcium (Ca) 1460 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 0.1 10 Iron (Fe) 0.572 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 0.1 10 Lithium (Li) 0.066 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 0.05 10 Magnesium (Mg) 552 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 0.05 10 Manganese (Mn) < 0.05 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 0.05 10 Potassium (K) 30.1 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 1 10 Sodium (Na) 78.7 mg/L EPA 200.7 8/28/2012 12:23:00 PM MHH7131 0.5 10 DISSOLVED METALS BY ICP-MS Selenium (Se) < 5 ug/L EPA 200.8 8/24/2012 2:37:00 PM KRICHAR 5 5 TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 Cadmium (Cd) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 Chromium (Cr) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 Copper (Cu) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 Nickel (Ni) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 Selenium (Se) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 Silver (Ag) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 Zinc (Zn) < 5 ug/L EPA 200.8 8/29/2012 1:32:00 PM KRICHAR 5 5 SELENIUM SPECIATION - (Analysis Performed by Applied Speciation and Consulting, LLC) Vendor Parameter Complete Vendor Method V_AS&C


### 2012018268 Collection Date: 20-Aug-12 8:45 AM 

### Site: BioReactor 2 Eff BLANK Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF MERCURY 1631 - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND MERCURY 1631 - DISSOLVED - (Analysis Performed by Brooks Rand Labs LLC) Vendor Parameter Complete Vendor Method V_BRAND

# Certificate of Laboratory Analysis This report shall not be re produced, exce pt in full. 

## Order # J12080361

2012018269 Collection Date: 20-Aug-12 11:30 AM 

### Site: Filter Blk Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sam p le #:

Analyst DF DISSOLVED METALS BY ICP Manganese (Mn) < 0.005 mg/L EPA 200.7 8/24/2012 10:26:00 AM DJSULL1 0.005 1 DISSOLVED METALS BY ICP-MS Selenium (Se) < 1 ug/L EPA 200.8 8/24/2012 1:27:00 PM KRICHAR 1 1

## September 12 , 201 2

Jay Perkins Duke Energy Analytical Laboratory Mail Code MGO3A2 (Building 7405) 13339 Hagers Ferry Rd. Huntersville, NC 28078 (704) 875-5 245 Project: Allen Shay/MillerCreek (LIMS #J12080361 )

Dear Mr. Perkins, Attached is the report associated with four (4) aqueous samples submitted for selenium speciation analysis on August 21 , 2012.The samples were received in a sealed cooler at0.7 ° C on August 22 , 2012

.Selenium speciation analysis was performed via ion chromatography inductively coupled plasma collision reaction cell mass spectrometry (IC-ICP-CRC -MS). Any issues associated with the analysis are addressed in the following report. If you have any questions, please feel free to contact me at your convenience.
Sincerely,

Ben Wozniak Project Manager Applied Speciation and Consulting, LLC

## Applied Speciation and Consulting, LLC Report prepared for: Jay Perkins Duke Energy Analytical Laboratory Mail Code MGO3A2 (Building 7405) 1 3339 Hagers Ferry Rd. Huntersville, NC 28078 Project: Allen Shay/MillerCreek (LIMS #J12080361)

September 12 , 2012

1. Sample Reception Four (4) aqueous samples in125mL HDPE bottles (provided by Applied Speciation and Consulting) were submitted for selenium speciation analysis on August 21 , 2012. The samples were received on August 22 , 201 2 in a sealed container at 0.7 ° C. The samples were received in a laminar flow clean hood,void of trace metals contamination and ultra-violet radiation, and were designated discrete sample identifiers. An aliquot of each sample was filtered (0.45μm) and each filtrate wasstored in a secure, monitored cryofreezer (maintained at a temperature of -80o

## C) until selenium speciation analysis could be performed via ion chromatography inductively coupled plasma collision reaction cell mass spectrometry (IC-ICP- CRC -MS).

2. Sample Preparation All sample preparation is performed in laminar flow clean hoods known to be free from trace metals contamination. All applied water for dilutions and sample preservatives are monitored for contamination to account for any biases associated with the sample results. Selenium Speciation Analysis by IC-ICP-CRC-MS Prior to analysis, an aliquot of each sample was filtered with a syringe filter (0.45μm) and injected directly into a sealed autosampler vial. No further sample preparation was performed as any chemical alteration of a sample may shift the equilibrium of the system, resulting in changes in speciation ratios.

3. Sample Analysis All sample analysis is preceded by a minimum of a five-point calibration curve spanning the entire concentration range of interest. Calibration curves are performed at the beginning of

## each analytical day. All calibration curves, associated with each species of interest, are

standardized by linear regression resulting in a response factor. All sample results are instrument blank correctedto account for any operational biases associated with the analytical platform. Prior to sample analysis, all calibration curves are verified using second source standards which are identified as initial calibration verification standards (ICV). Ongoing instrument performance is identified by the analysis of continuing calibration verification standards (CCV) and continuing calibration blanks (CCB) at a minimal interval of every ten analytical runs. Selenium Speciation Analysis by IC-ICP-CRC-MS Eachsample for selenium speciation analysis w asanalyzed by ion chromatography inductively coupled plasma collision reaction cell mass spectrometry (IC-ICP-CRC -MS) on August 29, 2012. An aliquot of eachsample is injected onto an anion exchange column and mobilized by a basic (pH > 7) gradient. The eluting selenium species are then introduced into a radio frequency (RF) plasma where energy-transfer processes cause desolvation, atomization, and ionization. The ions are extracted from the plasma through a differentially-pumped vacuum interface and travel through a pressurized chamber (CRC) containing a reaction gas which preferentially reacts with interfering ions of the same target mass to charge ratios (m/z). A solid-state detector detects ions transmitted through the mass analyzer and the resulting current is processed by a data handling system. Retention times for each eluting species are compared to known standards for species identification.

4. Analytical Issues The overall analyses went well and no significant analytical issues were encountered. All quality control parameters associated with the samples were within acceptance limits. The estimated method detection limits (eMDLs) for selenite, selenate, and selenocyanate are generated from replicate analyses of the lowest standard in the calibration curve. Not all selenium species are present in preparation blanks; therefore, eMDL calculations based on preparation blanks are artificially biased low. The eMDL for methylseleninic acid and selenomethionine is calculated from the average eMDL of selenite, selenate, and selenocyanate. The calibration does not contain methylseleninic acid or selenomethionine due to impurities in these standards which would bias the results for other selenium species.

## If you have any questions or concerns regarding this report, please feel free to contact me.

Sincerely,

Ben Wozniak Project Manager Applied Speciation and Consulting, LLC

### Sample Results
Sample ID Se(IV) Se(VI) SeCN MeSe(IV) SeMe Unknown Se Species (n) FGD Purge Eff ND (<6.8) 663 ND (<2.1) ND (<3.4) ND (<3.4) 0.0 (0) BioReactor 1 Inf ND (<1.7) 759 ND (<0.51) ND (<0.85) ND (<0.85) 0.0 (0) BioReactor 2 Inf 33.6 23.0 0.71 1.45 ND (<0.85) 0.0 (0) BioReactor 2 Eff ND (<1.7) ND (<0.34) ND (<0.51) ND (<0.85) ND (<0.85) 0.0 (0) All results reflect the applied dilution and are reported in μg/L ND = Not detected at the applied dilution SeCN = Selenocyanate MeSe(IV) = Methylseleninic acid SeMe = Selenomethionine Unknown Se Species = Total concentration of all unknown Se species observed by IC-ICP-MS n = number of unknown Se species observed Report Generated by: Ben Wozniak Applied Speciation and Consulting, LLC Selenium Speciation Results for Duke Energy Project Name: Allen Shay/MillerCreek Contact: Jay Perkins
Date: September 12, 2012 LIMS #J12080361Quality Control Summary - Preparation Blank Summary

Analyte (μg/L) PBW1 PBW2 PBW3 PBW4 Mean StdDev eMDL* eMDL 250x eMDL 1000x Se(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.0068 1.7 6.8 Se(VI) 0.016 0.000 0.000 0.000 0.004 0.008 0.0014 0.34 1.4 SeCN 0.000 0.000 0.000 0.000 0.000 0.000 0.0021 0.51 2.1 MeSe(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.0034 0.85 3.4 SeMe 0.000 0.000 0.000 0.000 0.000 0.000 0.0034 0.85 3.4 eMDL = Estimated Method Detection Limit *Please see narrative regarding eMDL calculations
Quality Control Summary - Certified Reference Materials Analyte (μg/L) CRM True Value Result Recovery Se(IV) LCS 9.57 9.47 99.0 Se(VI) LCS 9.48 9.33 98.4 SeCN LCS 8.92 8.63 96.7 MeSe(IV) LCS 6.47 6.14 95.0 SeMe LCS 9.32 8.81 94.5 Applied Speciation and Consulting, LLC Selenium Speciation Results for Duke Energy Project Name: Allen Shay/MillerCreek Contact: Jay Perkins LIMS #J12080361 Date: September 12, 2012 Report Generated by: Ben WozniakQuality Control Summary - Matrix Duplicates

Analyte (μg/L) Sample ID Rep 1 Rep 2 Mean RPD Se(IV) BioReactor 2 Inf 33.6 34.3 33.9 2.1 Se(VI) BioReactor 2 Inf 23.02 22.64 22.83 1.6 SeCN BioReactor 2 Inf 0.71 ND (<0.51) NC NC MeSe(IV) BioReactor 2 Inf 1.45 1.58 1.52 8.4 SeMe BioReactor 2 Inf ND (<0.85) ND (<0.85) NC NC ND = Not detected at the applied dilution NC = Value was not calculated due to one or more concentrations below the eMDL

Quality Control Summary - Matrix Spike/ Matrix Spike Duplicate Analyte (μg/L) Sample ID Spike Conc MS Result Recovery Spike Conc MSD Result Recovery RPD Se(IV) BioReactor 2 Inf 1390 1412 99.2 1390 1413 99.2 0.0 Se(VI) BioReactor 2 Inf 1261 1262 98.3 1261 1263 98.3 0.0 SeCN BioReactor 2 Inf 1144 1108 96.8 1144 1107 96.8 0.1 Applied Speciation and Consulting, LLC Selenium Speciation Results for Duke Energy Project Name: Allen Shay/MillerCreek Contact: Jay Perkins LIMS #J12080361 Date: September 12, 2012 Report Generated by: Ben Wozniak

### 3958 6 th

### Ave NW • Seattle, WA 98107 • T: 206-632-6206 • F: 206-632-6017 • www.brooksrand.com • brl@brooksrand.com 

## August 31, 2012 Duke Energy ATTN: Jay Perkins Scientific Support-Laboratory 13339 Hagers Ferry Road Huntersville NC 28078 jcperkins@duke-energy.com labcustomer@duke-energy.com RE: Project DUK-HV1201 Client Project: J12080361 Dear Mr. Perkins, On August 22, 2012, Brooks Rand Labs (BRL) received three (3) wastewater samples and three (3) corresponding field blanks. An aliquot was removed from each sample bottle and filtered into a separate container designed for dissolved mercury (Hg) analysis. The sample volume from the original container was logged-in for total Hg analysis. All samples were received, prepared, analyzed, and stored according to BRL SOPs and EPA methodology.Data used for regulatory purposes has a 24 hour filtration holding time requirement. Nonregulatory purposed data has a 48 hour filtration holding time. The results were blank-corrected as described in the calculations section of the relevant SOP(s) and may have been evaluated using reporting limits that have been adjusted to account for sample aliquot size. Please refer to the Sample Results page for sample-specific MDLs, MRLs, and other details. The instrument blank (IBL) IBL1 had an abnormal peak. The IBL was re-analyzed as IBL5 which produced a normal peak. IBL5 was reported in place of IBL1. All data was reported without qualification, aside from concentration qualifiers, and all associated quality control sample results met the acceptance criteria. BRL, an accredited laboratory, certifies the reported results of all analyses for which BRL is NELAP accredited meet all NELAP requirements. For more details, see the Report Information page of the report. Please feel free to contact me if you have any questions regarding this report. Sincerely,
Lydia Greaves Project Manager lydia@brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



### Definition of Data Qualifiers

(Effective 9/23/09) 

### Laboratory Accreditation BRL is accredited by the National Environmental Laboratory Accreditation Program (NELAP) through the State of Florida Department of Health, Bureau of Laboratories (E87982) and is certified to perform many environmental analyses. BRL is also certified by many other states to perform environmental analyses. For a current list of our accreditations /certifications, please visit our website at <http://www.brooksrand.com/default.asp?contentID=586>. Results reported relate only to the samples listed in the report. 

# Report Information

BLK BRL BS CAL CCV CRM D DUP ICV MSD ND NR PS REC RPD RSD SCV SOP 

### method blank Brooks Rand Labs laboratory fortified blank calibration standard continuing calibration verification certified reference material dissolved fraction duplicate initial calibration verification matrix spike duplicate non-detect non-reportable post preparation spike percent recovery relative percent difference relative standard deviation secondary calibration verification standard operating procedure MDL MRL MS



### method detection limit method reporting limit matrix spike

SRM T COC



### standard reference material total recoverable fraction chain of custody record 

### Common Abbreviations

These qualifiers are based on those previously utilized by Brooks Rand Labs, those found in the EPA SOW ILM03.0, Exhibit B, Section III, pg. B-18, and the USEPA Contract Laboratory Program National Functional Guidelines for Inorganic Superfund Data Review; USEPA; January 2010. These supersede all previous qualifiers ever employed by BRL. Detected by the instrument, the result is > the MDL but ≤the MRL. Result is reported and considered an estimate. B E 

### An estimated value due to the presence of interferences. A full explanation is presented in the narrative. H 

### Holding time and/or preservation requirements not met. Result is estimated. J 

### Estimated value. A full explanation is presented in the narrative. J-M 

### Duplicate precision (RPD) for associated QC sample was not within acceptance criteria. Result is estimated. J-N 

### Spike recovery for associated QC sample was not within acceptance criteria. Result is estimated. M 

### Duplicate precision (RPD) was not within acceptance criteria. Result is estimated. N 

### Spike recovery was not within acceptance criteria. Result is estimated. R 

### Rejected, unusable value. A full explanation is presented in the narrative. U 

### Result is ≤the MDL or client requested reporting limit (CRRL). Result reported as the MDL or CRRL. X 

### Result is not BLK-corrected and is within 10x the absolute value of the highest detectable BLK in the batch. Result is estimated. 

### Field Quality Control Samples Please be notified that certain EPA methods require the collection of field quality control samples of an appropriate type and frequency; failure to do so is considered a deviation from some methods and for compliance purposes should only be done with the approval of regulatory authorities. Please see the specific EPA methods for details regarding required field quality control samples.

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Sample Information

Report Matrix Type Received Sampled Sample Lab ID 

### 1234013-01 BioReactor 1 Inf 08/20/2012 08/22/2012 Sample Influent 1234013-02 BioReactor 1 Inf 08/20/2012 08/22/2012 Sample Influent 1234013-03 BioReactor 1 Inf Hg Blk 08/20/2012 08/22/2012 Field Blank DIW 1234013-04 BioReactor 1 Inf Hg Blk 08/20/2012 08/22/2012 Field Blank DIW 1234013-05 BioReactor 2 Inf 08/20/2012 08/22/2012 Sample Influent 1234013-06 BioReactor 2 Inf 08/20/2012 08/22/2012 Sample Influent 1234013-07 BioReactor 2 Inf Hg Blk 08/20/2012 08/22/2012 Field Blank DIW 1234013-08 BioReactor 2 Inf Hg Blk 08/20/2012 08/22/2012 Field Blank DIW 1234013-09 BioReactor 2 Eff 08/20/2012 08/22/2012 Sample Effluent 1234013-10 BioReactor 2 Eff 08/20/2012 08/22/2012 Sample Effluent 1234013-11 BioReactor 2 Eff Hg Blk 08/20/2012 08/22/2012 Field Blank DIW 1234013-12 BioReactor 2 Eff Hg Blk 08/20/2012 08/22/2012 Field Blank DIW 

# Batch Summary

Analyte Prepared Analyzed Sequence Batch Lab Matrix Method 

### B121527 08/24/2012 08/28/2012 1200668 Water EPA 1631 Hg

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Sample Results

Sample Sequence Result MDL MRL Unit Batch

Qualifier Analyte Basis

Report Matrix 

### BioReactor 1 Inf 

### 15100 T 1200668 B121527 Influent 135 50.5 1234013-01 Hg ng/L 14700 D 1200668 B121527 Influent 80.8 30.3 1234013-02 Hg ng/L
BioReactor 1 Inf Hg Blk 

### 0.15 T U 1200668 B121527 DIW 0.40 0.15 1234013-03 Hg ng/L 0.15 D U 1200668 B121527 DIW 0.41 0.15 1234013-04 Hg ng/L

BioReactor 2 Eff 

### 55.9 T 1200668 B121527 Effluent 4.04 1.52 1234013-09 Hg ng/L 10.2 D 1200668 B121527 Effluent 0.82 0.31 1234013-10 Hg ng/L
BioReactor 2 Eff Hg Blk 

### 0.15 T U 1200668 B121527 DIW 0.41 0.15 1234013-11 Hg ng/L 0.15 D U 1200668 B121527 DIW 0.40 0.15 1234013-12 Hg ng/L

BioReactor 2 Inf 

### 1920 T 1200668 B121527 Influent 40.8 15.3 1234013-05 Hg ng/L 49.9 D 1200668 B121527 Influent 0.81 0.30 1234013-06 Hg ng/L
BioReactor 2 Inf Hg Blk 

### 0.15 T U 1200668 B121527 DIW 0.41 0.15 1234013-07 Hg ng/L 0.15 D U 1200668 B121527 DIW 0.41 0.15 1234013-08 Hg ng/L

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Accuracy & Precision Summary

Batch: 

### B121527

Analyte Result Units Native Spike REC & Limits RPD & Limits Method: 

### EPA 1631 Lab Matrix: 

### Water

Sample Certified Reference Material (1232065, NIST 1641d 1000x dilution) B121527-SRM1 

### 15.68 106% ng/L 85-115 Hg 16.69
Matrix Spike (1234011-05) B121527-MS2 

### 5510 102% ng/L 71-125 Hg 6736

1103
Matrix Spike Duplicate (1234011-05) B121527-MSD2 

### 5510 109% ng/L 71-125 245% Hg 7098

1103
Matrix Spike (1234034-03) B121527-MS3 

### 3030 106% ng/L 71-125 Hg 3845

644.0
Matrix Spike Duplicate (1234034-03) B121527-MSD3 

### 3030 103% ng/L 71-125 242% Hg 3773

644.0

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Method Blanks & Reporting Limits

Batch: 

### B121527
Method: 

### EPA 1631 Matrix: 

### Water Analyte: 

### Hg Result Units Sample 

### B121527-BLK1 ng/L 0.14 B121527-BLK2 ng/L 0.10 B121527-BLK3 ng/L 0.08 B121527-BLK4 ng/L 0.12 MDL: 

### 0.15 Average: 

### 0.11 Standard Deviation: 

### 0.03 Limit: 

### 0.10 Limit: 

### 0.50 MRL: 

### 0.40

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Instrument Calibration

Sequence: 

### 1200668 Method: 

### EPA 1631 Instrument: 

### THG-06(MerxT) Date: 

### 08/28/2012 Total Mercury and Mercury Speciation by CVAFS

Analyte: 

### Hg REC & Limits Result True Value Lab ID Units 

### 1200668-IBL2 5.89 pg of Hg 1200668-IBL3 5.89 pg of Hg 1200668-IBL4 9.85 pg of Hg 1200668-CAL1 25.00 21.87 pg of Hg 87% 1200668-CAL2 100.0 105.0 pg of Hg 105% 1200668-CAL3 500.0 515.2 pg of Hg 103% 1200668-CAL4 2500 2614 pg of Hg 105% 1200668-CAL5 10000 10230 pg of Hg 102% 1200668-ICV1 1568 1669 pg of Hg 106% 85-115 1200668-CCV1 500.0 508.8 pg of Hg 102% 77-123 1200668-CCB1 9.43 pg of Hg 1200668-IBL5 6.15 pg of Hg 1200668-ICB1 6.87 pg of Hg 1200668-CCB2 44.4 pg of Hg 1200668-CCB3 11.2 pg of Hg 1200668-CCB4 8.20 pg of Hg 1200668-CCV2 500.0 513.5 pg of Hg 103% 77-123 1200668-CCV3 500.0 410.0 pg of Hg 82% 77-123 1200668-CCV4 500.0 548.0 pg of Hg 110% 77-123 1200668-CCV5 500.0 514.9 pg of Hg 103% 77-123

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Sample Containers

Lab ID: 

### 1234013-01 Report Matrix: 

### Influent Sample Type: 

### Sample Received: 

### 08/22/2012 Sample: 

### BioReactor 1 Inf Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71666330 10 Cooler

none n/a 500 mL Bottle FLPE Hg-T

Lab ID: 

### 1234013-02 Report Matrix: 

### Influent Sample Type: 

### Sample Received: 

### 08/22/2012 Sample: 

### BioReactor 1 Inf Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71659890 20 Cooler

none n/a 250 mL Bottle FLPE Hg-T
Comments: 

### Split from THg Container

Lab ID: 

### 1234013-03 Report Matrix: 

### DIW Sample Type: 

### Field Blank Received: 

### 08/22/2012 Sample: 

### BioReactor 1 Inf Hg Blk Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71666330 10 Cooler

none n/a 500 mL Bottle FLPE Hg-T

Lab ID: 

### 1234013-04 Report Matrix: 

### DIW Sample Type: 

### Field Blank Received: 

### 08/22/2012 Sample: 

### BioReactor 1 Inf Hg Blk Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71659890 20 Cooler

none n/a 250 mL Bottle FLPE Hg-T
Comments: 

### Split from THg Container

Lab ID: 

### 1234013-05 Report Matrix: 

### Influent Sample Type: 

### Sample Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Inf Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71666330 10 Cooler

none n/a 500 mL Bottle FLPE Hg-T

Lab ID: 

### 1234013-06 Report Matrix: 

### Influent Sample Type: 

### Sample Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Inf Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71659890 20 Cooler

none n/a 250 mL Bottle FLPE Hg-T
Comments: 

### Split from THg Container

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Sample Containers

Lab ID: 

### 1234013-07 Report Matrix: 

### DIW Sample Type: 

### Field Blank Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Inf Hg Blk Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71666330 10 Cooler

none n/a 500 mL Bottle FLPE Hg-T

Lab ID: 

### 1234013-08 Report Matrix: 

### DIW Sample Type: 

### Field Blank Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Inf Hg Blk Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71659890 20 Cooler

none n/a 250 mL Bottle FLPE Hg-T
Comments: 

### Split from THg Container

Lab ID: 

### 1234013-09 Report Matrix: 

### Effluent Sample Type: 

### Sample Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Eff Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71666330 10 Cooler

none n/a 500 mL Bottle FLPE Hg-T

Lab ID: 

### 1234013-10 Report Matrix: 

### Effluent Sample Type: 

### Sample Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Eff Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71659890 20 Cooler

none n/a 250 mL Bottle FLPE Hg-T
Comments: 

### Split from THg Container

Lab ID: 

### 1234013-11 Report Matrix: 

### DIW Sample Type: 

### Field Blank Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Eff Hg Blk Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71666330 10 Cooler

none n/a 500 mL Bottle FLPE Hg-T

Lab ID: 

### 1234013-12 Report Matrix: 

### DIW Sample Type: 

### Field Blank Received: 

### 08/22/2012 Sample: 

### BioReactor 2 Eff Hg Blk Collected: 

### 08/20/2012 Ship. Cont. pH P-Lot Preservation Lot Size Container Des 

### A 71659890 20 Cooler

none n/a 250 mL Bottle FLPE Hg-T
Comments: 

### Split from THg Container

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### Project ID: 

### DUK-HV1201

PM: 

### Tiffany Stilwater Client PM: 

### Jay Perkins Client PO: 

### 141391



# Shipping Containers

Cooler Tracking No: 

### 5353 0519 3373 via FedEx Temperature: 

### -0.6 °C Coolant Type: 

### Ice Description: 

### Cooler Damaged in transit? 

### No Returned to client? 

### No Custody seals present? 

### No Custody seals intact? 

### No COC present? 

### Yes Received: 

### August 22, 2012 8:50

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com

### This data package contains the analytical results for the project identified above and includes a Case Narrative, Sample Results and Chain of Custody. Unless otherwise noted, all samples were received in acceptable condition and processed according to the referenced methods. Data qualifiers are flagged individually on each sample. A key reference for the data qualifiers appears at the end of this case narrative. NC Certification No. 402 SC Certification No. 99012 NC Drinking Water Cert No. 37735 

# Case Narrative 08/27/2012

Duke Energy Corporation (04) Jay Perkins 13339 Hagers Ferry Road Huntersville, NC 28078 Project: Allen Shay/Miller Creek Project No.: J12080361 Lab Submittal Date: 08/21/2012 Prism Work Order: 2080548 VA Certification No. 1287



### Please call if you have any questions relating to this analytical report. Respectfully, PRISM LABORATORIES, INC.



### VP Laboratory Services Reviewed By

Data Qualifiers Key Reference: 

### HT Sample received and analyzed outside of the hold time.

Method Detection Limit MDL Below Reporting Limit BRL
Relative Percent Difference RPD


## * Results reported to the reporting limit. All other results are reported to the MDL with values between MDL and reporting limit indicated with a J.

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 1 of 9

# Sample Receipt Summary 08/27/2012 

### Prism Work Order: 2080548 Client Sample ID Matrix Lab Sample ID Date Sampled Date Received 

### 2080548-01 08/20/12 2012018261/FGD Purge Eff 08/21/12 Water 2080548-02 08/20/12 2012018263/BioReactor 1 Inf 08/21/12 Water 2080548-03 08/20/12 2012018265/BioReactor 2 Inf 08/21/12 Water 2080548-04 08/20/12 2012018267/BioReactor 2 Eff 08/21/12 Water Samples received in good condition at 2.9 degrees C unless otherwise noted.

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 2 of 9

# Laboratory Report 08/27/2012

Result Parameter Batch ID Report Limit Analysis Date/Time Method Dilution Factor Units MDL Analyst 

### 13339 Hagers Ferry Road Project No.: Project: Allen Shay/Miller Creek Duke Energy Corporation (04)

Huntersville, NC 28078 Attn: Jay Perkins Sample Matrix: Water Client Sample ID: Prism Sample ID: 2080548-01 Prism Work Order: 2080548 Time Collected: 08/20/12 08:15 Time Submitted: 08/21/12 17:05 2012018261/FGD Purge Eff


### J12080361

General Chemistry Parameters 7.2 *SM4500-H B P2H0516 1 8/23/12 11:00 JAB HT pH Units pH 52 *SM2320 B P2H0512 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Total Alkalinity BRL *SM2320 B P2H0513 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Carbonate Alkalinity 52 *SM2320 B P2H0514 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Bicarbonate Alkalinity

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc. 449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 3 of 9

# Laboratory Report 08/27/2012

Result Parameter Batch ID Report Limit Analysis Date/Time Method Dilution Factor Units MDL Analyst 

### 13339 Hagers Ferry Road Project No.: Project: Allen Shay/Miller Creek Duke Energy Corporation (04)

Huntersville, NC 28078 Attn: Jay Perkins Sample Matrix: Water Client Sample ID: Prism Sample ID: 2080548-02 Prism Work Order: 2080548 Time Collected: 08/20/12 08:40 Time Submitted: 08/21/12 17:05 2012018263/BioReactor 1 Inf


### J12080361

General Chemistry Parameters 7.0 *SM4500-H B P2H0516 1 8/23/12 11:00 JAB HT pH Units pH 47 *SM2320 B P2H0512 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Total Alkalinity BRL *SM2320 B P2H0513 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Carbonate Alkalinity 47 *SM2320 B P2H0514 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Bicarbonate Alkalinity

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc. 449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 4 of 9

# Laboratory Report 08/27/2012

Result Parameter Batch ID Report Limit Analysis Date/Time Method Dilution Factor Units MDL Analyst 

### 13339 Hagers Ferry Road Project No.: Project: Allen Shay/Miller Creek Duke Energy Corporation (04)

Huntersville, NC 28078 Attn: Jay Perkins Sample Matrix: Water Client Sample ID: Prism Sample ID: 2080548-03 Prism Work Order: 2080548 Time Collected: 08/20/12 08:50 Time Submitted: 08/21/12 17:05 2012018265/BioReactor 2 Inf


### J12080361

General Chemistry Parameters 7.4 *SM4500-H B P2H0516 1 8/23/12 11:00 JAB HT pH Units pH 260 *SM2320 B P2H0512 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Total Alkalinity BRL *SM2320 B P2H0513 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Carbonate Alkalinity 260 *SM2320 B P2H0514 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Bicarbonate Alkalinity

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc. 449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 5 of 9

# Laboratory Report 08/27/2012

Result Parameter Batch ID Report Limit Analysis Date/Time Method Dilution Factor Units MDL Analyst 

### 13339 Hagers Ferry Road Project No.: Project: Allen Shay/Miller Creek Duke Energy Corporation (04)

Huntersville, NC 28078 Attn: Jay Perkins Sample Matrix: Water Client Sample ID: Prism Sample ID: 2080548-04 Prism Work Order: 2080548 Time Collected: 08/20/12 08:45 Time Submitted: 08/21/12 17:05 2012018267/BioReactor 2 Eff


### J12080361

General Chemistry Parameters 7.4 *SM4500-H B P2H0516 1 8/23/12 11:00 JAB HT pH Units pH 230 *SM2320 B P2H0512 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Total Alkalinity BRL *SM2320 B P2H0513 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Carbonate Alkalinity 230 *SM2320 B P2H0514 1 5.0 8/23/12 11:00 JAB mg/L 0.66 Bicarbonate Alkalinity

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc. 449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 6 of 98/27/12 

### Level II QC Report

13339 Hagers Ferry Road Project No: J12080361 Project: Allen Shay/Miller Creek Duke Energy Corporation (04)

Huntersville, NC 28078 Attn: Jay Perkins Prism Work Order: 2080548 Time Submitted: 8/21/2012 5:05:00PM

Result Limit

Reporting Units Level Spike Result

Source %REC %REC Limits RPD RPD Limit Notes Analyte General Chemistry Parameters - Quality Control



### Batch P2H0512 - NO PREP Blank (P2H0512-BLK1) Prepared & Analyzed: 08/23/12 Total Alkalinity mg/L BRL 5.0 LCS (P2H0512-BS1) Prepared & Analyzed: 08/23/12 Total Alkalinity mg/L 242 5.0 250.0 90-110 97 LCS Dup (P2H0512-BSD1) Prepared & Analyzed: 08/23/12 Total Alkalinity mg/L 246 5.0 250.0 200 90-110 98 2 Duplicate (P2H0512-DUP1) Prepared & Analyzed: 08/23/12 Source: 2080548-04 Total Alkalinity mg/L 224 5.0 228 20 2 

### Batch P2H0513 - NO PREP Blank (P2H0513-BLK1) Prepared & Analyzed: 08/23/12 Carbonate Alkalinity mg/L BRL 5.0 LCS (P2H0513-BS1) Prepared & Analyzed: 08/23/12 Carbonate Alkalinity mg/L 242 5.0 90-110 LCS Dup (P2H0513-BSD1) Prepared & Analyzed: 08/23/12 Carbonate Alkalinity mg/L 246 5.0 200 90-110 2 Duplicate (P2H0513-DUP1) Prepared & Analyzed: 08/23/12 Source: 2080548-04 Carbonate Alkalinity mg/L BRL 5.0 BRL 20 

### Batch P2H0514 - NO PREP Blank (P2H0514-BLK1) Prepared & Analyzed: 08/23/12 Bicarbonate Alkalinity mg/L BRL 5.0

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 7 of 98/27/12 

### Level II QC Report

13339 Hagers Ferry Road Project No: J12080361 Project: Allen Shay/Miller Creek Duke Energy Corporation (04)

Huntersville, NC 28078 Attn: Jay Perkins Prism Work Order: 2080548 Time Submitted: 8/21/2012 5:05:00PM

Result Limit

Reporting Units Level Spike Result

Source %REC %REC Limits RPD RPD Limit Notes Analyte General Chemistry Parameters - Quality Control



### Batch P2H0514 - NO PREP LCS (P2H0514-BS1) Prepared & Analyzed: 08/23/12 Bicarbonate Alkalinity mg/L 242 5.0 250.0 90-110 97 LCS Dup (P2H0514-BSD1) Prepared & Analyzed: 08/23/12 Bicarbonate Alkalinity mg/L 246 5.0 250.0 200 90-110 98 2 Duplicate (P2H0514-DUP1) Prepared & Analyzed: 08/23/12 Source: 2080548-04 Bicarbonate Alkalinity mg/L 224 5.0 228 20 2 

### Batch P2H0516 - NO PREP LCS (P2H0516-BS1) Prepared & Analyzed: 08/23/12 pH pH Units 6.81 6.860 99-101 99

This report should not be reproduced, except in its entirety, without the written consent of Prism Laboratories, Inc.

449 Springbrook Road - P.O. Box 240543 - Charlotte, NC 28224-0543 Phone: 704/529-6364 - Toll Free Number: 1-800/529-6364 - Fax: 704/525-0409 

### Page 8 of 9

### Page 9 of 9