| ARTICLE      1 | –      DEFINITIONS  | 2 |
|----------------|--------------------------------|---|

| ARTICLE      2 | –      INTERPRETATION  | 16 |
|----------------|-----------------------------------|----|

| ARTICLE      3 | –      SCOPE OF WORK  | 17 |
|----------------|----------------------------------|----|

|   | 3.1 | General  | 17 |
|--------|-----|---------------|----|

|   | 3.2 | Phases      of the Work  | 17 |
|--------|-----|-------------------------------|----|

|   | 3.3 | Project      Schedule  | 18 |
|--------|-----|-----------------------------|----|

|   | 3.4 | Not      Used  | 18 |
|--------|-----|---------------------|----|

|   | 3.5 | Contractor      Responsibilities  | 19 |
|--------|-----|----------------------------------------|----|

|   | 3.6 | Owner's      Responsibilities  | 21 |
|--------|-----|-------------------------------------|----|

|   | 3.7 | Subcontractors  | 23 |
|--------|-----|----------------------|----|

| ARTICLE      4 | –      FACILITY LICENSES, PERMITS ANDAPPROVALS27 |
|----------------|--------------------------------------------------------|

|   | 4.1 | Owner      Permits  | 27 |
|--------|-----|--------------------------|----|

|   | 4.2 | Contractor      Permits  | 28 |
|--------|-----|-------------------------------|----|

|   | 4.3 | ITAACs  | 28 |
|--------|-----|--------------|----|

| ARTICLE      5 | –      QUALITY ASSURANCE  | 28 |
|----------------|--------------------------------------|----|

|   | 5.1 | Quality      Assurance  | 28 |
|--------|-----|------------------------------|----|

|   | 5.2 | Reporting      of Defects, Noncompliance, Failures and Breakdowns of QA      Programs  | 29 |
|--------|-----|---------------------------------------------------------------------------------------------|----|

|   | 5.3 | Quality      Control and Inspection Activities  | 30 |
|--------|-----|------------------------------------------------------|----|

|   | 5.4 | Access      and Auditing at Contractor Facilities  | 30 |
|--------|-----|---------------------------------------------------------|----|

|   | 5.5 | Access      and Audits at Subcontractors' Facilities  | 30 |
|--------|-----|------------------------------------------------------------|----|

|   | 5.6 | Witness      and Hold Points  | 31 |
|--------|-----|------------------------------------|----|

|   | 5.7 | Owner's      Right to Inspect and Stop Work  | 32 |
|--------|-----|---------------------------------------------------|----|

| ARTICLE      6 | –      CONTRACT PRICE  | 32 |
|----------------|-----------------------------------|----|

|   | 6.1 | Components      of the Contract Price  | 32 |
|--------|-----|---------------------------------------------|----|

|   | 6.2 | [**]  | 32 |
|--------|-----|------------|----|

|   | 6.3 | [**]  | 33 |
|--------|-----|------------|----|

| ARTICLE      7 | –      PRICE ADJUSTMENT PROVISIONS  | 34 |
|----------------|------------------------------------------------|----|

| ARTICLE      8 | –      PAYMENTS  | 34 |
|----------------|-----------------------------|----|

|   | 8.1 | [**]  | 34 |
|--------|-----|------------|----|

|   | -i- |   |
|--------|-----|--------|

|   | 8.2 | Milestone      Payments  | 35 |
|--------|-----|-------------------------------|----|

|   | 8.3 | Final      Payment  | 35 |
|--------|-----|--------------------------|----|

|   | 8.4 | Supporting      Documentation; Payment Disputes  | 36 |
|--------|-----|-------------------------------------------------------|----|

|   | 8.5 | No      Acceptance by Payment  | 37 |
|--------|-----|-------------------------------------|----|

|   | 8.6 | Security      for Payment and Performance  | 37 |
|--------|-----|-------------------------------------------------|----|

|   | 8.7 | Separate      Payments for Consortium Members  | 38 |
|--------|-----|-----------------------------------------------------|----|

| ARTICLE      9 | –      CHANGES IN THE WORK  | 38 |
|----------------|----------------------------------------|----|

|   | 9.1 | Entitlement      to Change Order  | 38 |
|--------|-----|----------------------------------------|----|

|   | 9.2 | Owner-Directed      Changes  | 39 |
|--------|-----|-----------------------------------|----|

|   | 9.3 | Effect      of Changes  | 39 |
|--------|-----|------------------------------|----|

|   | 9.4 | Change      Orders  | 40 |
|--------|-----|--------------------------|----|

|   | 9.5 | Disputes      over Changes  | 41 |
|--------|-----|----------------------------------|----|

|   | 9.6 | Changes      for Contractor's Convenience  | 41 |
|--------|-----|-------------------------------------------------|----|

|   | 9.7 | Optional      Services and Equipment  | 42 |
|--------|-----|--------------------------------------------|----|

|   | 9.8 | [**]  | 42 |
|--------|-----|------------|----|

| ARTICLE      10 | –      UNCONTROLLABLE CIRCUMSTANCES  | 42 |
|-----------------|-------------------------------------------------|----|

|   | 10.1 | Performance      Excused  | 42 |
|--------|------|--------------------------------|----|

|   | 10.2 | Notice  | 42 |
|--------|------|--------------|----|

| ARTICLE      11 | –      TESTING  | 43 |
|-----------------|----------------------------|----|

|   | 11.1 | Scope      and Objective of Testing  | 43 |
|--------|------|-------------------------------------------|----|

|   | 11.2 | Construction      and Installation Tests  | 43 |
|--------|------|------------------------------------------------|----|

|   | 11.3 | Preoperational      System Tests  | 44 |
|--------|------|----------------------------------------|----|

|   | 11.4 | Startup      Tests Objectives and Protocol  | 45 |
|--------|------|--------------------------------------------------|----|

|   | 11.5 | Performance      Tests  | 47 |
|--------|------|------------------------------|----|

|   | 11.6 | Net      Unit Electrical Output Guarantee  | 49 |
|--------|------|-------------------------------------------------|----|

| ARTICLE      12 | –      STAGES OF COMPLETION  | 51 |
|-----------------|-----------------------------------------|----|

|   | 12.1 | Turnover  | 51 |
|--------|------|----------------|----|

|   | 12.2 | Preoperational      Test Completion  | 52 |
|--------|------|-------------------------------------------|----|

|   | 12.3 | Startup      Test Completion  | 52 |
|--------|------|------------------------------------|----|

|   | 12.4 | Substantial      Completion  | 53 |
|--------|------|-----------------------------------|----|

|   | -ii- |   |
|--------|------|--------|

|   | 12.5 | Punch      List  | 53 |
|--------|------|-----------------------|----|

|   | 12.6 | Final      Completion  | 53 |
|--------|------|-----------------------------|----|

| ARTICLE      13 | –      [**]  | 54 |
|-----------------|-------------------------|----|

|   | 13.1 | [**]  | 54 |
|--------|------|------------|----|

|   | 13.2 | [**]  | 55 |
|--------|------|------------|----|

|   | 13.3 | [**]  | 55 |
|--------|------|------------|----|

|   | 13.4 | [**]  | 55 |
|--------|------|------------|----|

| ARTICLE      14 | –      WARRANTY  | 56 |
|-----------------|-----------------------------|----|

|   | 14.1 | Equipment  | 56 |
|--------|------|-----------------|----|

|   | 14.2 | Services      Warranty  | 60 |
|--------|------|------------------------------|----|

|   | 14.3 | Warranty      of Title  | 60 |
|--------|------|------------------------------|----|

|   | 14.4 | [**]  | 61 |
|--------|------|------------|----|

|   | 14.5 | [**]  | 62 |
|--------|------|------------|----|

|   | 14.6 | [**]  | 62 |
|--------|------|------------|----|

| ARTICLE      15 | –      INDEMNITY  | 62 |
|-----------------|------------------------------|----|

|   | 15.1 | Contractor      Indemnity  | 62 |
|--------|------|---------------------------------|----|

|   | 15.2 | Owner's      Indemnity  | 63 |
|--------|------|------------------------------|----|

|   | 15.3 | [**]  | 63 |
|--------|------|------------|----|

|   | 15.4 | [**]  | 64 |
|--------|------|------------|----|

|   | 15.5 | [**]  | 65 |
|--------|------|------------|----|

| ARTICLE      16 | –      INSURANCE  | 66 |
|-----------------|------------------------------|----|

|   | 16.1 | Phase      I Insurance Requirements  | 66 |
|--------|------|-------------------------------------------|----|

|   | 16.2 | Phase      II Insurance Requirements  | 67 |
|--------|------|--------------------------------------------|----|

|   | 16.3 | Provisions      Applicable to all Coverages  | 69 |
|--------|------|---------------------------------------------------|----|

| ARTICLE      17 | –      [**]  | 70 |
|-----------------|-------------------------|----|

|   | 17.1 | [**]  | 70 |
|--------|------|------------|----|

|   | 17.2 | [**]  | 70 |
|--------|------|------------|----|

|   | 17.3 | [**]  | 71 |
|--------|------|------------|----|

| ARTICLE      18 | –      LIENS  | 71 |
|-----------------|--------------------------|----|

|   | 18.1 | Liens  | 71 |
|--------|------|-------------|----|

|   | -iii- |   |
|--------|-------|--------|

|   | 18.2 | Discharge      or Bond  | 71 |
|--------|------|------------------------------|----|

| ARTICLE      19 | –      PROPRIETARY DATA  | 72 |
|-----------------|-------------------------------------|----|

|   | 19.1 | Protection      of Owner Proprietary Data  | 72 |
|--------|------|-------------------------------------------------|----|

|   | 19.2 | Protection      of Contractor's Proprietary Data  | 73 |
|--------|------|--------------------------------------------------------|----|

|   | 19.3 | Special      Procedures Pertaining to Contractor's Proprietary  Data75 |
|--------|------|------------------------------------------------------------------------|

|   | 19.4 | Ownership      of Rights in Documentation  | 79 |
|--------|------|-------------------------------------------------|----|

|   | 19.5 | Ownership      of Invention Rights  | 79 |
|--------|------|------------------------------------------|----|

|   | 19.6 | Software  | 80 |
|--------|------|----------------|----|

|   | 19.7 | Publicity  | 80 |
|--------|------|-----------------|----|

| ARTICLE      20 | –      ENVIRONMENTAL; HAZARDOUS MATERIALS  | 80 |
|-----------------|-------------------------------------------------------|----|

|   | 20.1 | Material      Safety Data Sheets  | 80 |
|--------|------|----------------------------------------|----|

|   | 20.2 | Facility      Use, Storage Removal  | 80 |
|--------|------|------------------------------------------|----|

|   | 20.3 | Handling,      Collection, Removal Transportation and Disposal  | 80 |
|--------|------|----------------------------------------------------------------------|----|

|   | 20.4 | Notice      of Discovery  | 81 |
|--------|------|--------------------------------|----|

| ARTICLE      21 | –      TITLE; RISK OF LOSS  | 81 |
|-----------------|----------------------------------------|----|

|   | 21.1 | Transfer      of Title  | 81 |
|--------|------|------------------------------|----|

|   | 21.2 | Risk      of Loss  | 81 |
|--------|------|-------------------------|----|

|   | 21.3 | [**]  | 82 |
|--------|------|------------|----|

| ARTICLE      22 | –      SUSPENSION AND TERMINATION  | 82 |
|-----------------|-----------------------------------------------|----|

|   | 22.1 | Suspension      by the Owner for Convenience  | 82 |
|--------|------|----------------------------------------------------|----|

|   | 22.2 | Termination      by Owner for Cause  | 83 |
|--------|------|-------------------------------------------|----|

|   | 22.3 | Termination      by Owner for Convenience  | 84 |
|--------|------|-------------------------------------------------|----|

|   | 22.4 | Suspension      and Termination Due to Other Circumstances  | 84 |
|--------|------|------------------------------------------------------------------|----|

|   | 22.5 | Termination      by Contractor  | 86 |
|--------|------|--------------------------------------|----|

|   | 22.6 | Actions      Required of Contractor upon Termination  | 87 |
|--------|------|------------------------------------------------------------|----|

| ARTICLE      23 | –      SAFETY; INCIDENT REPORTING  | 87 |
|-----------------|-----------------------------------------------|----|

|   | 23.1 | Environmental,      Health and Safety Programs  | 87 |
|--------|------|------------------------------------------------------|----|

|   | 23.2 | Designated      Contractor Safety Representative  | 87 |
|--------|------|--------------------------------------------------------|----|

|   | 23.3 | OSHA      and Other Laws  | 88 |
|--------|------|--------------------------------|----|

|   | 23.4 | Worksite      Safety  | 89 |
|--------|------|----------------------------|----|

|   | -iv- |   |
|--------|------|--------|

|   | 23.5 | Dangerous      Materials  | 89 |
|--------|------|--------------------------------|----|

|   | 23.6 | Cooperation      in Governmental Investigations and Inspections  | 89 |
|--------|------|-----------------------------------------------------------------------|----|

|   | 23.7 | Audit  | 89 |
|--------|------|-------------|----|

| ARTICLE      24 | –      QUALIFICATIONS AND PROTECTION OF ASSIGNED PERSONNEL  | 90 |
|-----------------|------------------------------------------------------------------------|----|

|   | 24.1 | Screening      Measures  | 90 |
|--------|------|-------------------------------|----|

|   | 24.2 | Contractor's      Personnel  | 90 |
|--------|------|-----------------------------------|----|

|   | 24.3 | Training      of Employees  | 91 |
|--------|------|----------------------------------|----|

|   | 24.4 | NRC      Whistleblower Provision  | 91 |
|--------|------|----------------------------------------|----|

|   | 24.5 | Respirator      Protection  | 91 |
|--------|------|----------------------------------|----|

| ARTICLE      25 | –      RECORDS AND AUDIT  | 91 |
|-----------------|--------------------------------------|----|

|   | 25.1 | Technical      Documentation  | 91 |
|--------|------|------------------------------------|----|

|   | 25.2 | Accounting      Records  | 92 |
|--------|------|-------------------------------|----|

|   | 25.3 | Maintenance      of Records Generally  | 92 |
|--------|------|---------------------------------------------|----|

|   | 25.4 | Right      to Audit  | 92 |
|--------|------|---------------------------|----|

|   | 25.5 | Sales      Tax Records  | 92 |
|--------|------|------------------------------|----|

| ARTICLE      26 | –      TAXES  | 93 |
|-----------------|--------------------------|----|

|   | 26.1 | Employment      Taxes  | 93 |
|--------|------|-----------------------------|----|

|   | 26.2 | Sales      and Use Taxes on Contractor Tools  | 93 |
|--------|------|----------------------------------------------------|----|

|   | 26.3 | Sales      and Use Tax on Equipment  | 93 |
|--------|------|-------------------------------------------|----|

|   | 26.4 | State      Property Taxes  | 93 |
|--------|------|---------------------------------|----|

|   | 26.5 | Tax      Indemnification  | 94 |
|--------|------|--------------------------------|----|

|   | 26.6 | Pollution      Control Equipment Information  | 94 |
|--------|------|----------------------------------------------------|----|

|   | 26.7 | Non-resident      Contractor  | 94 |
|--------|------|------------------------------------|----|

| ARTICLE      27 | –      DISPUTE RESOLUTION  | 94 |
|-----------------|---------------------------------------|----|

|   | 27.1 | Claims  | 94 |
|--------|------|--------------|----|

|   | 27.2 | Change      Dispute  | 95 |
|--------|------|---------------------------|----|

|   | 27.3 | Resolution      by Negotiation  | 95 |
|--------|------|--------------------------------------|----|

|   | 27.4 | Mediation  | 96 |
|--------|------|-----------------|----|

|   | 27.5 | Arbitration      of Claims[**]  | 96 |
|--------|------|--------------------------------------|----|

|   | -v- |   |
|--------|-----|--------|

|   | 27.6 | Exclusive      Resolution Procedures; Equitable Remedies  | 98 |
|--------|------|----------------------------------------------------------------|----|

|   | 27.7 | Consent      to Jurisdiction  | 98 |
|--------|------|------------------------------------|----|

|   | 27.8 | Continuation      of Work  | 99 |
|--------|------|---------------------------------|----|

| ARTICLE      28 | –      NOTICES  | 99 |
|-----------------|----------------------------|----|

| ARTICLE      29 | –      ASSIGNMENT  | 101 |
|-----------------|-------------------------------|-----|

| ARTICLE      30 | –      WAIVER  | 101 |
|-----------------|---------------------------|-----|

| ARTICLE      31 | –      MODIFICATION  | 101 |
|-----------------|---------------------------------|-----|

| ARTICLE      32 | –      SURVIVAL  | 101 |
|-----------------|-----------------------------|-----|

| ARTICLE      33 | –      TRANSFER  | 101 |
|-----------------|-----------------------------|-----|

| ARTICLE      34 | –      GOVERNING LAW; WAIVER OF JURY TRIAL; CERTAIN FEDERAL      LAWS  | 102 |
|-----------------|-----------------------------------------------------------------------------------|-----|

|   | 34.1 | Governing      Law  | 102 |
|--------|------|--------------------------|-----|

|   | 34.2 | Waiver      of Jury Trial  | 102 |
|--------|------|---------------------------------|-----|

|   | 34.3 | Certain      Federal Laws  | 102 |
|--------|------|---------------------------------|-----|

| ARTICLE      35 | –      RELATIONSHIP OF OWNER ANDCONTRACTOR102 |
|-----------------|-----------------------------------------------------|

| ARTICLE      36 | –      THIRD PARTY BENEFICIARIES  | 102 |
|-----------------|----------------------------------------------|-----|

| ARTICLE      37 | –      REPRESENTATIONS AND WARRANTIES  | 103 |
|-----------------|---------------------------------------------------|-----|

|   | 37.1 | Representations      and Warranties of Contractor  | 103 |
|--------|------|---------------------------------------------------------|-----|

|   | 37.2 | Representations      and Warranties of SCE&G and SanteeCooper103 |
|--------|------|----------------------------------------------------------------------|

| ARTICLE      38 | –      MISCELLANEOUS PROVISIONS  | 104 |
|-----------------|---------------------------------------------|-----|

|   | 38.1 | Rights      Exclusive  | 104 |
|--------|------|-----------------------------|-----|

|   | 38.2 | Severability  | 104 |
|--------|------|--------------------|-----|

|   | 38.3 | Entire      Agreement  | 105 |
|--------|------|-----------------------------|-----|

|   | 38.4 | Counterparts  | 105 |
|--------|------|--------------------|-----|

|   | -vi- |   |
|--------|------|--------|

| Exhibit | Description of      Exhibit                                                |
|---------|----------------------------------------------------------------------------|
| A       | Scope      of Work/Supply and Division of Responsibilities                 |
| B       | Contractor      Organization Chart                                         |
| C       | Owner      and Contractor Permits                                          |
| D       | Project      Execution Plan Processes                                      |
| E       | Project      Schedule                                                      |
| F-1     | Milestone      Payment Schedule                                            |
| F-2     | Payment      Plan                                                          |
| G       | [**]                                                                       |
| H       | Pricing                                                                    |
| I-1     | Toshiba      Parent Guaranty                                               |
| I-2     | Shaw      Parent Guaranty                                                  |
| J       | Price      Adjustment Provisions                                           |
| K       | Costs                                                                      |
| L       | Net      Electric Guarantee Conditions and Load List                       |
| M-1     | Software      License                                                      |
| M-2     | AP1000      Intellectual Property License (WEC)                            |
| M-3     | AP1000      Intellectual Property License (S&W)                        |
| N       | Industry      Codes and Standards                                          |
| O-1     | Proprietary      Data Agreement                                            |
| O-2     | List      of Intellectual Property Subject to Third Party License    Terms |
| P-1     | Major      Subcontractors                                                  |
| P-2     | Subcontractors      for Site Construction and Related Field Services       |
| Q       | Equipment      with Owner-Designated Witness and Hold Points               |
| R       | Description      of Site                                                   |
| S       | EEO      and Small Business Regulations                                    |
| T       | [Not      Used]                                                            |
| U       | OCIP      Description                                                      |
| V       | Limited      Agency Agreement                                              |
| W       | [**]      Special Terms                                                    |
|    |                                                                       |

| ·   | Cleaning      and flushing |
|--------------------|----------------------------|

| ·   | Hydrostatic      testing |
|--------------------|--------------------------|

| ·   | Checks      of electrical wiring |
|--------------------|----------------------------------|

| ·   | Valve      testing |
|--------------------|--------------------|

| ·   | Energization      and operation of equipment |
|--------------------|----------------------------------------------|

| ·   | Calibration      of instrumentation |
|--------------------|-------------------------------------|

| ·   | Demonstrate      that essential plant components and systems, including alarms and      indications, meet appropriate requirements based on the      design. |
|--------------------|--------------------------------------------------------------------------------------------------------------------------------------------------------------|

| ·   | Provide      documentation of the performance and condition of the components and      systems. |
|--------------------|-------------------------------------------------------------------------------------------------|

| ·   | Provide      baseline test and operating data on equipment and systems for future use      and reference. |
|--------------------|-----------------------------------------------------------------------------------------------------------|

| ·   | Operate      Equipment for a sufficient period to demonstrate performance in accordance      with the Preoperational Testprocedures. |
|--------------------|--------------------------------------------------------------------------------------------------------------------------------------|

| ·   | Demonstrate      that the systems operate on an integratedbasis. |
|--------------------|------------------------------------------------------------------|

| ·   | Tests      related to initial Nuclear Fuelloading. |
|--------------------|----------------------------------------------------|

| ·   | Tests      performed after initial Nuclear Fuel loading but prior to initial      criticality. |
|--------------------|------------------------------------------------------------------------------------------------|

| ·   | Tests      related to initial criticality and those performed at low power (less than      five percent (5%)). |
|--------------------|---------------------------------------------------------------------------------------------------------------------|

| ·   | Tests      performed at power levels greater than five percent  (5%) |
|--------------------|----------------------------------------------------------------------|

| ·   | Install      the Nuclear Fuel in the Unit reactor vessel in a controlled and safe      manner. |
|--------------------|------------------------------------------------------------------------------------------------|

| ·   | Verify      that the Unit reactor core and components, equipment, and systems required      for control and shutdown have been assembled according to design and meet      specified performance requirements. |
|--------------------|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| ·   | Achieve      initial criticality and operation at power in a controlled and safe      manner. |
|--------------------|-----------------------------------------------------------------------------------------------|

| ·   | Verify      that the operating characteristics of the Unit reactor core and associated      control and protection equipment are consistent with design requirements      and accident analysis assumptions. |
|--------------------|--------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| ·   | Obtain      the required data and calibrate equipment used to control and protect the      Facility. |
|--------------------|------------------------------------------------------------------------------------------------------|

| ·   | Verify      that the Unit responds to the transient tests as described in the Design      Control Document. |
|--------------------|-------------------------------------------------------------------------------------------------------------|

| ·   | Verify      the operating characteristics of the Unit secondary plant equipment      (turbine, generator, isophase bus duct and main power transformer, heater      balance, main steam, extraction steam, steam dump, condenser, condensate,      feedwater, make-up water, cooling tower, main feedwater pumps, etc.) and      associated control equipment. |
|--------------------|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| [**] | [**] |
|------|------|
| [**] | [**] |
| [**] | [**] |
| [**] | [**] |
| [**] | [**] |
| [**] | [**] |

| ·   | Prohibition      of the use, transportation, sale, or possession of illegal      drugs |
|--------------------|----------------------------------------------------------------------------------------|

| ·   | Prohibition      of the use or possession of alcohol beverages on the  Site |
|--------------------|-----------------------------------------------------------------------------|

| ·   | Requirement      that employees be fit for duty at all times while on the    Site |
|--------------------|-----------------------------------------------------------------------------------|

| ·   | Requirement      that employees submit to drug and alcohol testing during preaccess      screening, for-cause testing, and post event testing, as      necessary |
|--------------------|------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| ·   | Requirement      that all employees must immediately report known, suspected, or potential      violations of this policy to supervisory personnel or      management |
|--------------------|-----------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| ·   | Requirement      that a subset of workers who perform important safety functions be subject      to random testing |
|--------------------|--------------------------------------------------------------------------------------------------------------------|

| ·   | Protection      of information and records to assure  confidentiality |
|--------------------|-----------------------------------------------------------------------|

| ·   | Requirement      that employees consent to a search or inspection of the individual's      property while on the Site. |
|--------------------|------------------------------------------------------------------------------------------------------------------------|

| ·   | Verification      of identity |
|--------------------|-------------------------------|

| ·   | A      criminal history check of the individual shall be  performed |
|--------------------|---------------------------------------------------------------------|

| ·   | Prior      to a final adverse determination, the applicant shall be informed of the      basis for potential denial of access to the Site to assure the accuracy of      the basis for such denial. |
|--------------------|-----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| SOUTH      CAROLINA ELECTRIC & GAS COMPANY, for itself and as agent for South      Carolina Public Service AuthorityBy:/s/ William B.      TimmermanName: William B.      TimmermanTitle: President and      CEO |                                                                                                                   |
|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|------------------------------------------------------------------------------------------------------------------------|
| STONE      & WEBSTER, INC.By: /s/ David P.      BarryName:David P. BarryTitle: Executive Vice      President                                                                                                     | WESTINGHOUSE      ELECTRIC COMPANY LLCBy:/s/ Aris      CandrisName: Aris      CandrisTitle: Senior Vice      President |

EXHIBIT A

| Listing      of Required Permits and Licenses                                                                                                                                                                                                                                                                                   |
|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|
| PERMITS,      PLANS, & DETERMINATIONS NEEDED                                                                                                                                                                                                                                                                                | PERMITTYPE | DESIGN DATA NEEDED      (Y/N) | DEVELOP    PERMIT | OWNER      /  HOLDER | IMPLEMENT      PERMIT |
| Well      Permit (Groundwater Wells)(SC      R61-71)                                                                                                                                                                                                                                                                            |  State      DHEC | Y | X | X | X |
| Negative      declaration on cultural resources from the State Historic Preservation      Officer (SHPO)(36      CFR Part 800)                                                                                                                                                                                                  |  State | N | N/A | N/A | N/A |
| Negative      declaration on endangered species from the U.S. Fish and Wildlife Services      (USFWS)(50      CFR Parts 13, 17, 222, 226, 227, 402, 424, 450-453)                                                                                                                                                               | Federal | N/A | N/A | N/A | N/A |
| Negative      declaration on endangered species from South Carolina Department of      Natural Resources (SCDNR)(50      CFR Parts 13, 17, 222, 226, 227, 402, 424, 450-453)                                                                                                                                                    | State | N/A | N/A | N/A | N/A |
| Wetlands      404 Permit from U.S. Army Corps of Engineers (COE)(33      CFR 328)                                                                                                                                                                                                                                               | Federal | Y | O/X | O | X |
| Floodplain      Assessment(E.O.      11988)                                                                                                                                                                                                                                                                                     | Federal | N/A | N/A | N/A | N/A |
| Federal      Aviation Administration § 77.15 Permit(14      CFR 77)                                                                                                                                                                                                                                                        | Federal | Y | X | X | X |
| PERMITS,      PLANS, & DETERMINATIONS NEEDED FOR ANY CONSTRUCTION                                                                                                                                                                                                                                                           |
| Air      Quality Protection Permitting                                                                                                                                                                                                                                                                                          |
| DOE      Spent Fuel Agreement/Contract (NWPA 1982)                                                                                                                                                                                                                                                                              | Federal | N | O | O | O |
| Bureau      of Air Quality Construction Permit(May      include contractor small sources)(SC      R. 61-62)                                                                                                                                                                                                                     | State      DHEC | Y | O/X | O | X |
| Concrete      Batch Plant BAQ Permit (Form IIF)(May      be part of BAQ Construction Permit)(SC      R. 61-62)                                                                                                                                                                                                                  | State      DHEC | Y | O/X | O | X |
| Surface      Water Protection Permitting                                                                                                                                                                                                                                                                                        |
| Dam      Repair/Alterations Permit(SC      R. 72-1 through R. 72-9)                                                                                                                                                                                                                                                             | State      DHEC | N/A | N/A | N/A | N/A |
| Water      Use Permit (Water withdrawal from Broad River)                                                                                                                                                                                                                                                                       | Federal | N/A | N/A | N/A | N/A |
| Sec      401 Water Quality Certification (SCDHEC)(SC      R61-101)                                                                                                                                                                                                                                                              | State | Y | O/X | O | X |
| Public      Water Supply System (Potable Water)(SC      R. 61-58.)                                                                                                                                                                                                                                                              | State      DHEC | Y | O/X | O | X |
| Sec      404 Dredge & Fill Permit (Corps of Engineers)Dredging      of Ponds and River (33 CFR 323)Construction      in Wetlands (33 CFR 330)Wetland      and/or stream fillConstruction      of Intake/Discharge Structures (33 CFR 322/Section 10 Rivers and Harbors      Act)and Impact to Navigable Waters (33 USC 403) | Federal/State | Y | O/X | O | X |
| County      Septic Tank Permit                                                                                                                                                                                                                                                                                                  | County | N/A | N/A | N/A | N/A |
| NPDES      Permit to ConstructSanitary      WastewaterWastewater      TreatmentIntake      Structure (33 CFR 322)Discharge      structure (SC      R. 61-9)                                                                                                                                                                | State      DHEC | Y | O/X | O | X |
| NPDES      Permit - Concrete Batch Plant(SC      R. 61-9)                                                                                                                                                                                                                                                                       | State      DHEC | Y | O/X | O | X |
| NPDES      Stormwater PermitConstruction      Storm Water Pollution Prevention Plan (SWPPP)Erosion      Control PlanGrading      PermitNotice      of Intent (NOI)(SC      R. 61-9)                                                                                                                                             | State      DHEC | Y | O/X | O | X |
| CZMA      Approval / Waiver                                                                                                                                                                                                                                                                                                     | State/Federal | Y | O | O | O |
| Facility      Response Plan for Oil Spills(40      CFR 112, SC R. 61-9 BMP)                                                                                                                                                                                                                                                     | State | N/A | N/A | N/A | N/A |
| Groundwater/Drinking      Water Protection Permitting                                                                                                                                                                                                                                                                           |
| Diesel      Fuel Storage Tank (UST) Installation Permit (Potentially not required for      above ground tanks)(SC      R. 61-92)                                                                                                                                                                                                | State      DHEC | N/A | N/A | N/A | N/A |
| Waste      Management Permitting                                                                                                                                                                                                                                                                                                |
| Construction      & Demolition Landfill(SC      R. 61-71, R. 61-107.258, R. 61-107.11, and R. 61-107.13)                                                                                                                                                                                                                    | State      DHEC | Y | O/X | O | X |
| Pollution      Prevention and Waste Minimization Plan (RCRA)(SC      R. 61-79, and SC R. 61-104)                                                                                                                                                                                                                                | State      DHEC | N/A | N/A | N/A | N/A |
| Process      Waste Disposal/RCRA ID Number(SC      R. 61-79, and SC R. 61-104)                                                                                                                                                                                                                                                  | State      DHEC | Y | O/X | O | X |
| Used      Oil Disposal(SC      R. 61-79, and SC R. 61-104)                                                                                                                                                                                                                                                                      | State | N/A | N/A | N/A | N/A |
| Miscellaneous      Permits                                                                                                                                                                                                                                                                                                      |
| NRC      COL                                                                                                                                                                                                                                                                                                                    | NRC | N/A | N/A | N/A | N/A |
| FERC      License Revision (Project 1894)                                                                                                                                                                                                                                                                                  | FERC      License | Y | O/X | O | O |
| ASME      Owners Certification (NCA-3230)                                                                                                                                                                                                                                                                                       | ASME | N/A | O | O | O |
| Parr/FFPS      and Railroad Easements                                                                                                                                                                                                                                                                                           | SCE&G | Y | O/X | O | O |
| SC      Business License                                                                                                                                                                                                                                                                                                        | State | N/A | N/A | N/A | N/A |
| Release      from “Land Application” status for areas in and aroundL50.                                                                                                                                                                                                                                             | State      DHEC | N/A | N/A | N/A | N/A |
| Engineering      Report [International Building Codes, Sec 1704)(Fairfield      Co Building Safety)                                                                                                                                                                                                                             | County | Y | X | X | X |
| Building      Permit [Offices & warehouses only](Fairfield      Co Building Safety)                                                                                                                                                                                                                                         | County | Y | X | X | X |
| DOT      Highway Encroachment/Modifications                                                                                                                                                                                                                                                                                     | StateDOT | N/A | N/A | N/A | N/A |
| Blasting      Permit                                                                                                                                                                                                                                                                                                            | State | N | X | X | X |
| Certificate      of Public Convenience and Necessity(SC      Public Service Commission)                                                                                                                                                                                                                                         | State | Y | O/X | O | O |
| PERMITS,      PLANS, & DETERMINATIONS NEEDED FOR OPERATION                                                                                                                                                                                                                                                                  |
| Air      Quality Protection Permitting                                                                                                                                                                                                                                                                                          |
| Title      V Air Operating Permit or Conditional Major Source Permit(SC      R. 61-62)                                                                                                                                                                                                                                          | StateDHEC | Y | O/X | O | O |

| Listing      of Required Permits and Licenses                                                                                                |
|----------------------------------------------------------------------------------------------------------------------------------------------|
| PERMITS,      PLANS, & DETERMINATIONS NEEDED                                                                                             | PERMITTYPE | DESIGN DATA NEEDED      (Y/N) | DEVELOP    PERMIT | OWNER      /  HOLDER | IMPLEMENT      PERMIT |
| Surface      Water Protection Permitting                                                                                                     |
| NPDES      PermitSanitary      Wastewater DischargeWastewater      Treatment DischargeCooling      Tower Blowdown Discharge(SC      R. 61-9) | StateDHEC | Y | O/X | O | O |
| Operations      SPCC Plan(40      CFR 112, SC R. 61-9)                                                                                       | State | Y | N/A | N/A | N/A |
| NPDES      Operations Stormwater PermitOperations      Storm Water Pollution Prevention Plan (SWPPP)(SC      R. 61-9)                        | StateDHEC | Y | O/X | O | O |
| Groundwater/Drinking      Water Protection Permitting                                                                                        |
| Diesel      Fuel Storage Tank (UST) Operating Permit (Potentially not required for      above ground tanks)(SC      R. 61-92)                | StateDHEC | N/A | N/A | N/A | N/A |

| Listing      of Required Permits and Licenses                                             |
|-------------------------------------------------------------------------------------------|
| PERMITS,      PLANS, & DETERMINATIONS NEEDED                                          | PERMITTYPE | DESIGN DATA NEEDED      (Y/N) | DEVELOP    PERMIT | OWNER      /  HOLDER | IMPLEMENT      PERMIT |
| Waste      Management Permitting                                                          |
| Process      Waste Disposal/RCRA ID Number(SC      R. 61-79, and SC R. 61-104)            | State | Y | O/X | O | O |
| Pollution      Prevention and Waste Minimization Plan(SC      R. 61-79, and SC R. 61-104) | State | Y | O/X | O | O |
| Radioactive      Materials/Transport License(SC      R 61-63 and R 61-83)                 | State      DHEC | N | O | O | O |
| SNM      License10      CFR 30, 40 and 70                                                 | FederalNRC | N | O | O | O |
| Certificate      to Transport Hazardous Materials(40      CFR and SC R 61-79)             | Federal/DOT | N | O | O | O |

|   | SMACNA      – Sheet Metal and Air Conditioning Contractors National      Association                                                                    22 |
|--------|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

|                   UBC – Uniform Building Code |                                                                                         22 |
|-----------------------------------------------------------------------------------------------------------------|----------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| ACI      - American Concrete Institute                                                                                                                                                                                                                                                                                                                                                                                                                                                                     |                    |
|------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|-------------------------|
| ACI      117, “Standard Specification for Tolerances for Concrete Construction and      Materials,” 1990                                                                                                                                                                                                                                                                                                                                                                                       | 3.8                     |
| ACI      211.1, “Standard Practice for Selecting Proportions for Normal, Heavy      Weight, and Mass Concrete,” 1991                                                                                                                                                                                                                                                                                                                                                                           | 3.8                     |
| ACI      304R, “Guide for Measuring, Mixing, Transporting, and Placing Concrete,”      2000                                                                                                                                                                                                                                                                                                                                                                                                    | 3.8                     |
| ACI      318, “Building Code Requirements for Reinforced Concrete,”      2002                                                                                                                                                                                                                                                                                                                                                                                                                  | 2.5                     |
| ACI      349.3R, “Evaluation of Existing Nuclear Safety-Related Concrete      Structures,” 1996                                                                                                                                                                                                                                                                                                                                                                                                | 3.8                     |
| ACI      349, “Code Requirements for Nuclear Safety Related Concrete Structures,”      2001                                                                                                                                                                                                                                                                                                                                                                                                    | 1A,      3.8, 3H        |
| AISC      - American Institute of Steel Construction                                                                                                                                                                                                                                                                                                                                                                                                                                                       |                    |
| AISC      N690, “Specification for the Design, Fabrication, and Erection of Steel      Safety-Related Structures for Nuclear Facilities,” 1994                                                                                                                                                                                                                                                                                                                                                 | 3A,      3F, 3H         |
| AISC      S335, “Specification for Structural Steel Buildings, Allowable Stress      Design and Plastic Design,” 1989                                                                                                                                                                                                                                                                                                                                                                          | 3.3                     |
| Seismic      Provisions for Structural Steel Buildings, American Institute of Steel      Construction, April 1977 including Supplement 2, November    2000                                                                                                                                                                                                                                                                                                                                                 | 3.7                     |
| AISI      - American Iron and Steel Institute                                                                                                                                                                                                                                                                                                                                                                                                                                                              |                    |
| AISI,      “Specification for the Design of Cold Formed Steel Structural Members,”      1996 Edition and Supplement No. 1, July 30, 1999                                                                                                                                                                                                                                                                                                                                                       | 3A,      3F             |
| AMCA      - Air Movement and Control Association, Inc.                                                                                                                                                                                                                                                                                                                                                                                                                                                     |                    |
| AMCA      210, “Laboratory Method of Testing Fans for Rotating Purposes,”      1985                                                                                                                                                                                                                                                                                                                                                                                                            | 9.4                     |
| AMCA      211, “Certified Ratings Program Air Performance,” 1987                                                                                                                                                                                                                                                                                                                                                                                                                               | 9.4                     |
| AMCA      300, “Reverberant Room Method for Sound Testing of Fans,”    1985                                                                                                                                                                                                                                                                                                                                                                                                                    | 9.4                     |
| AMCA      500, “Test Method for Louvers, Dampers, and Shutters,”1989                                                                                                                                                                                                                                                                                                                                                                                                                           | 9.4                     |
| ANS      – American Nuclear Society                                                                                                                                                                                                                                                                                                                                                                                                                                                                  |                    |
| ANS      5.1, “Decay Heat Power in Light Water Reactors,” 1994                                                                                                                                                                                                                                                                                                                                                                                                                                 | 5.4                     |
| ANS      5.1, “Decay Heat Power in Light Water Reactor,” 1979                                                                                                                                                                                                                                                                                                                                                                                                                                  | 1.9,      15.2          |
| ANS      5.4, “American National Standard Method for Calculating the Fractional      Release of Volatile Fission Products From Oxide Fuel,”1982                                                                                                                                                                                                                                                                                                                                                | 1A                      |
| ANS      6.1, “Guidelines on the Nuclear Analysis and Design of Concrete Radiation      Shielding for Nuclear Power Plants,” 1989                                                                                                                                                                                                                                                                                                                                                              | 12.3                    |
| ANS      6.4, “Guidelines on the Nuclear Analysis and Design of Concrete Radiation      Shielding for Nuclear Power Plants,” 1997                                                                                                                                                                                                                                                                                                                                                              | 1A,      12.3           |
| ANS      15.8, “Nuclear Material Control Systems for Nuclear Power Plants,”      1974                                                                                                                                                                                                                                                                                                                                                                                                          | 13                      |
| ANS      18.1, “Radioactive Source Term for Normal Operation of Light Water      Reactors,” 1999                                                                                                                                                                                                                                                                                                                                                                                               | 1A,      11.1           |
| ANS      51.1, “Nuclear Safety Criteria for the Design of Stationary Pressurized      Water Reactor Plants,” 1983                                                                                                                                                                                                                                                                                                                                                                              | 3.2,      3.9, 5.4, 9.3 |
| ANS      55.6, “Liquid Radioactive Waste Processing Systems for Light Water Reactor      Plants,” 1993                                                                                                                                                                                                                                                                                                                                                                                         | 11.2                    |
| ANS      56.2, “Containment Isolation Provisions for Fluid Systems,”      1984                                                                                                                                                                                                                                                                                                                                                                                                                 | 1A                      |
| ANS      56.11, “Design Criteria for Protection Against the Effects of Compartment      Flooding in Light Water Reactor Plants,” 1988                                                                                                                                                                                                                                                                                                                                                          | 3.4                     |
| ANS      57.1, “Design Requirements for Light Water Reactor Fuel Handling Systems,”      1992                                                                                                                                                                                                                                                                                                                                                                                                  | 9.1                     |
| ANS      57.2, “Design Requirements for Light Water Reactor Spent Fuel Storage      Facilities at Nuclear Power Plants,” 1983                                                                                                                                                                                                                                                                                                                                                                  | 4.3,      9.1           |
| ANS      57.3, “Design Requirements for New Fuel Storage Facilities at LWR Plants,”      1983                                                                                                                                                                                                                                                                                                                                                                                                  | 4.3                     |
| ANS      58.2, “Design Bases for Protection of Light Water Nuclear Power Plants      Against Effects of Postulated Pipe Rupture,” 1988                                                                                                                                                                                                                                                                                                                                                         | 3.6                     |
| ANS      58.8, “Time Response Design Criteria for Nuclear Safety Related Operator      Actions,” 1984                                                                                                                                                                                                                                                                                                                                                                                          | 1.9                     |
| ANS      C-2, “National Electrical Safety Codes,” 1997                                                                                                                                                                                                                                                                                                                                                                                                                                         | 8.2                     |
| ANSI      – American National Standards Institute                                                                                                                                                                                                                                                                                                                                                                                                                                                    |                    |
| ANSI      16.1, “Nuclear Criticality Safety in Operations with Fissionable Materials      Outside Reactors,” 1975                                                                                                                                                                                                                                                                                                                                                                              | 9.1                     |
| ANSI      56.5, “PWR and BWR Containment Spray System Design Criteria,”      1979                                                                                                                                                                                                                                                                                                                                                                                                              | 1.9                     |
| ANSI      56.8, “Containment System Leakage Testing Requirements,”    1994                                                                                                                                                                                                                                                                                                                                                                                                                     | 6.2                     |
| ANSI      58.6, “Criteria for Remote Shutdown for Light Water Reactors,”      1996                                                                                                                                                                                                                                                                                                                                                                                                             | 7.4                     |
| ANSI      B16.34, “Valves – Flanged and Buttwelding End,” 1996                                                                                                                                                                                                                                                                                                                                                                                                                           | 3.2                     |
| ANSI      B16.41, “Functional Operational Requirement for Power Operated Valves,”      1983                                                                                                                                                                                                                                                                                                                                                                                                    | 1.9                     |
| ANSI      B30.2, “Overhead and Gantry Cranes,” 1990                                                                                                                                                                                                                                                                                                                                                                                                                                            | 9.1                     |
| ANSI      B30.9, “Slings,” 1996                                                                                                                                                                                                                                                                                                                                                                                                                                                                | 9.1                     |
| ANSI      B31.1, “Power Piping, ASME Code for Pressure Piping,” 1989                                                                                                                                                                                                                                                                                                                                                                                                                           | 3.2,      3.6, 9.2      |
| ANSI      B96.1, “Welded Aluminum-Alloy Storage Tanks,” 1981                                                                                                                                                                                                                                                                                                                                                                                                                                   | 3.2                     |
| ANSI      HFS-100, “American Standard for Human Factors Engineering of Visual      Display Terminal Workstations,” 1988                                                                                                                                                                                                                                                                                                                                                                        | 18.8                    |
| ANSI      N14.6, "Special Lifting Devices for Shipping Containers Weighing 10,000      pounds (4500 kg) or More,” 1993                                                                                                                                                                                                                                                                                                                                                                               | 3.9,      9.1           |
| ANSI      N16.1, “Nuclear Criticality Safety in Operations with Fissionable      Materials Outside Reactors,” 1975                                                                                                                                                                                                                                                                                                                                                                             | 9.1                     |
| ANSI      N16.9, “Validation of Calculational Methods for Nuclear Criticality      Safety,” 1975                                                                                                                                                                                                                                                                                                                                                                                               | 9.1                     |
| ANSI      N18.2, “Nuclear Safety Criteria for the Design of Stationary Pressurized      Water Reactor Plants,” 1973                                                                                                                                                                                                                                                                                                                                                                            | 15.0                    |
| ANSI      N18.2a, “Nuclear Safety Criteria for the Design of Stationary Pressurized      Water Reactor Plants,” 1975.                                                                                                                                                                                                                                                                                                                                                                          | 3.2                     |
| ANSI      N101.6, “Atomic Industry Facility Design, Construction, and Operation      Criteria,” 1972                                                                                                                                                                                                                                                                                                                                                                                           | 1A                      |
| ANSI      N210, “Design Objectives for Light Water Reactor Spent Fuel Storage      Facilities at Nuclear Power Stations,” 1976                                                                                                                                                                                                                                                                                                                                                                 | 9.1                     |
| ANSI      N237, “Source Term Specification,” 1976                                                                                                                                                                                                                                                                                                                                                                                                                                              | 1A                      |
| ANSI      N271, “Containment Isolation Provisions for Fluid Systems,”      1976                                                                                                                                                                                                                                                                                                                                                                                                                | 1A                      |
| ANSI      N278.1, “Self-Operated and Power-Operated Safety-Relief Valves Functional      Specification Standard,” 1975                                                                                                                                                                                                                                                                                                                                                                         | 5.4                     |
| API      – American Petroleum Institute                                                                                                                                                                                                                                                                                                                                                                                                                                                              |                    |
| API      610, “Centrifugal Pumps for General Refinery Services,”    1981                                                                                                                                                                                                                                                                                                                                                                                                                       | 3.2                     |
| API-620,      “Recommended Rules for Design and Construction of Large, Welded,      Low-Pressure Storage Tanks,” Revision 1, April 1985.                                                                                                                                                                                                                                                                                                                                                       | 3.2                     |
| API-650,      “Welded Steel Tanks for Oil Storage,” Revision 1, February      1984.                                                                                                                                                                                                                                                                                                                                                                                                            | 3.2                     |
| ARI      410, “Forced Circulation Air Cooling and Air Heating Coils”,      1991                                                                                                                                                                                                                                                                                                                                                                                                                | 9.4                     |
| ARI      – Air Conditioning and Refrigeration Institute                                                                                                                                                                                                                                                                                                                                                                                                                                              |                    |
| ARI      620, “Self-Contained Humidifiers for Residential Applications,”      1996                                                                                                                                                                                                                                                                                                                                                                                                             | 9.4                     |
| ASCE      – American Society of Civil Engineers                                                                                                                                                                                                                                                                                                                                                                                                                                                      |                    |
| ASCE      4, “Seismic Analysis of Safety-Related Nuclear Structures and Commentary,”      1989                                                                                                                                                                                                                                                                                                                                                                                                 | 3.7                     |
| ASCE      7, “Minimum Design Loads for Buildings and Other Structures,”      1998                                                                                                                                                                                                                                                                                                                                                                                                              | 3.7                     |
| ASCE      8, “Specification for the Design of Cold Formed Stainless Steel Structural      Members,” 1990                                                                                                                                                                                                                                                                                                                                                                                       | 6.2                     |
| ASCE      Paper No. 3269 “Wind Forces on Structures” Transactions of the American      Society of Civil Engineers, Vol. 126, Part II (1961)                                                                                                                                                                                                                                                                                                                                                    | 3                       |
| ASHRAE      – American Society of Heating, Refrigeration, and Air Conditioning      Engineers                                                                                                                                                                                                                                                                                                                                                                                                        |                    |
| ASHRAE      33, “Methods of Testing for Rating Forced Circulation Air Cooling and Air      Heating Coils,” 1978                                                                                                                                                                                                                                                                                                                                                                                | 9.4                     |
| ASHRAE      52.1 “Gravimetric and Dust Spot Procedures for Testing Air-Cleaning      Devices Used in General Ventilation for Removing Particulate Matter,”      1992                                                                                                                                                                                                                                                                                                                           | 9.4                     |
| ASHRAE      62, “Ventilation for Acceptable Indoor Air Quality,” 1999                                                                                                                                                                                                                                                                                                                                                                                                                          | 9.4                     |
| ASHRAE      62, “Ventilation for Acceptable Indoor Air Quality,” 1989                                                                                                                                                                                                                                                                                                                                                                                                                          | 6.4                     |
| ASHRAE      126, “Method of Testing HVAC Air Ducts,” 2000                                                                                                                                                                                                                                                                                                                                                                                                                                      | 9.4                     |
| ASME      – American Society of Mechanical Engineers                                                                                                                                                                                                                                                                                                                                                                                                                                                 |                    |
| ASME      OM Code, “Code for Operation and Maintenance of Nuclear Power Plants,”      1995 Edition, 1996 Addenda                                                                                                                                                                                                                                                                                                                                                                               | 3.9                     |
| ASME/ANSI      AG-1, “Code on Nuclear Air and Gas Treatment,” 1997                                                                                                                                                                                                                                                                                                                                                                                                                             | 1A,      3.2, 3A, 9.4   |
| ASME      B16.34, “Valves – Flanged and Buttwelding End,” 1996                                                                                                                                                                                                                                                                                                                                                                                                                           | 5.4                     |
| ASME      B30.2, “Overhead & Gantry Cranes,” 1990                                                                                                                                                                                                                                                                                                                                                                                                                                          | 9.1                     |
| ASME      B31.1, “Code for Power Piping,” 1989 Edition, 1989 Addenda                                                                                                                                                                                                                                                                                                                                                                                                                           | 5.2                     |
| ASME      Boiler and Pressure Vessel Code, Section II, “Metal Specifications”, 1989      Edition, 1989Addenda, (Class 1, 2, 3 Piping andComponents)                                                                                                                                                                                                                                                                                                                                            | 5.2,      5.4           |
| ASME      Boiler and Pressure Vessel Code, Section III, Rules for Construction of      Nuclear Power Plant Components, (The baseline used for the evaluations      done to support this safety analysis report and the Design Certification      is the 1998 Edition, 2000 Addenda, except as follows:  the 1989      Edition, 1989 Addenda is used for Articles NB-3200, NB-3600, NC-3600, and      ND-3600 in lieu of later editions and addenda.), (Class 1, 2, 3 Piping and      Components) | 3.9,      5.2, 5.3, 5.4 |
| Code      Case N-4-11, “Special Type 403 Modified Forgings or Bars, Section III,      Division 1, Class 1 and Class CS”                                                                                                                                                                                                                                                                                                                                                                        | 5.2                     |
| Code      Case N-20-4, “SB-163 Nickel-Chromium-Iron Tubing (Alloys 600 and 690) and      Nickel-Iron-Chromium Alloy 800 at a Specified Minimum Yield Strength      of 40.0 ksi and Cold Worked Alloy 800 at Yield Strength of 47.0 ksi,      Section III, Division 1, Class 1”                                                                                                                                                                                                            | 5.2                     |
| Code Case N-60-5, “Material for Core Support      Structures, Section III, Division 1”                                                                                                                                                                                                                                                                                                                                                                                                         | 5.2                     |
| Code      Case N-71-18, “ Additional Material for Subsection NF, Class 1, 2, 3 and      MC Component Supports Fabricated by Welding, Section III Division      1”                                                                                                                                                                                                                                                                                                                              | 5.2                     |
| Code      Case N-122-2 “Stress Indices for Integral Structural Attachments Section      III, Division 1, Class 1” 1994                                                                                                                                                                                                                                                                                                                                                                         | 5.2                     |
| Code      Case N-249-14, “Additional Materials for Subsection NF, Class 1, 2, 3, and      MC Supports Fabricated Without Welding, Section III, Division      1”                                                                                                                                                                                                                                                                                                                                | 5.2                     |
| Code      Case N-284-1, “Metal Containment Shell Buckling Design Methods, Section      III, Division 1 Class MC”                                                                                                                                                                                                                                                                                                                                                                               | 5.2                     |
| Code      Case N-318-5, “Procedure for Evaluation of the Design of Rectangular Cross      Section Attachments on Class 2 or 3 Piping Section III,      Division”                                                                                                                                                                                                                                                                                                                               | 5.2                     |
| Code      Case N-391-2, “Procedure for Evaluation of the Design of Hollow Circular      Cross Section Welded Attachments on Class 1 Piping Section III, Division      1”                                                                                                                                                                                                                                                                                                                       | 5.2                     |
| Code      Case N-319-3,  “Procedure for Evaluation of Stresses in Butt      Welding Elbows in Class 1 Piping, Section III, Division 1”                                                                                                                                                                                                                                                                                                                                               | 5.2                     |
| Code      Case N-392-3, “Procedure for Valuation of the Design of Hollow Circular      Cross Section Welded Attachments on Class 2 and 3 Piping Section III,      Division 1”                                                                                                                                                                                                                                                                                                                  | 5.2                     |
| Code  Case-N-474-2,      “Design Stress Intensities and Yield Strength Values for UNS06690 With a      Minimum Yield Strength of 35 ksi, Class 1 Components, Section III,      Division 1”                                                                                                                                                                                                                                                                                           | 5.2                     |
| ASME      Boiler and Pressure Vessel Code, Section IV, “Non-destructive      Examination,” 1998 Edition, 2000 Addenda, (Class 1, 2, 3 Piping and      Components)                                                                                                                                                                                                                                                                                                                              | 5.2                     |
| ASME      Boiler and Pressure Vessel Code, Section V, “Non-destructive Examination,”      1998 Edition, 2000 Addenda, (Class 1, 2, 3 Piping and      Components)                                                                                                                                                                                                                                                                                                                               | 5.4                     |
| ASME      Boiler and Pressure Vessel Code, Section VIII, Division 1, “Pressure      Vessels,” 1998 Edition, 2000 Addenda, (Class 1, 2, 3 Piping and      Components)                                                                                                                                                                                                                                                                                                                           | 5.2,      9.3           |
| ASME      Boiler and Pressure Vessel Code, Section IX, “Welding and Brazing      Qualifications,” 1998 Edition, 2000 Addenda, (Class 1, 2, 3 Piping and      Components)                                                                                                                                                                                                                                                                                                                       | 5.2                     |
| Code      Case 2142-1, “F-Number Grouping for Ni-Cr-Fe, Classification UNS N06052      Filler Metal, Section IX”                                                                                                                                                                                                                                                                                                                                                                               | 5.2                     |
| Code      Case 2143-1, “F-Number Grouping for Ni-Cr-Fe, Classification UNS W86152      Welding Electrode, Section IX”                                                                                                                                                                                                                                                                                                                                                                     | 5.2                     |
| ASME      Code Section XI (1998 Edition) and mandatory      appendices.  (Design provisions, in accordance with Section XI,      Article IWA-1500, are incorporated in the design processes for      Class 1 components.) , (Class 1, 2, 3 Piping and      Components)                                                                                                                                                                                                                      | 3.9,      5.2, 5.4      |
| ASME      Code Section XI (1996 Edition) Appendix G                                                                                                                                                                                                                                                                                                                                                                                                                                                        | 5.3                     |
| ASME      N509 (R1996), “Nuclear Power Plant Air Cleaning Units and Components,”      1989                                                                                                                                                                                                                                                                                                                                                                                                     | 1A,      3A, 9.4        |
| ASME      N510, “Testing of Nuclear Air Cleaning Systems,” 1989                                                                                                                                                                                                                                                                                                                                                                                                                                | 1A,      9.4            |
| ASME      NOG-1, “Rules for Construction of Overhead and Gantry Cranes (Top Running      Bridge, Multiple Girder),” ASME Code, Section IV, Pt. HWL,      1998.                                                                                                                                                                                                                                                                                                                                 | 9.1                     |
| ASME  NQA-1,      “Quality Management System,” 1989 edition through NQA-1b-1991,      Addenda(DCD      identifies NQA-1 1b 1991 Addenda, however NRC has accepted NQA-1 through      NQA-1c-1992, Addenda as acceptable via Reg Guide      1.28.  NQA-1-1c-1992 is to be specified to be consistent with      the ASME Section III Code and Addenda specified in the    DCD.)                                                                                              | 17.0                    |
| ASME      Performance Test Code 19.11, 1970                                                                                                                                                                                                                                                                                                                                                                                                                                                                | 10.4                    |
| ASTM      – American Society of Testing and Materials                                                                                                                                                                                                                                                                                                                                                                                                                                                |                    |
| ASTM      A 580, “Specification for Stainless and Heat-resisting Steel Wire,”      1990                                                                                                                                                                                                                                                                                                                                                                                                        | 4.2                     |
| ASTM      A 609, “Standard Specification for Longitudinal Beam Ultrasonic Inspection      of Carbon and Low Alloy Steel Castings,” 1991                                                                                                                                                                                                                                                                                                                                                        |                    |
| ASTM      A 615, “Deformed and Plain Billet Steel Bars for Concrete Reinforcement,”      2001                                                                                                                                                                                                                                                                                                                                                                                                  | 3.8                     |
| ASTM      A 706, “Low Alloy Steel Deformed Bars for Concrete Reinforcement,”      2001                                                                                                                                                                                                                                                                                                                                                                                                         | 3.8                     |
| ASTM      A 970, “Specification for Welded Headed Bars for Concrete Reinforcement,”      1998                                                                                                                                                                                                                                                                                                                                                                                                  | 3.8                     |
| ASTM      C 33, “Specification for Concrete Aggregates,” 2002                                                                                                                                                                                                                                                                                                                                                                                                                                  | 3.8                     |
| ASTM      C 94, “Specifications for Ready-Mixed Concrete,” 2000                                                                                                                                                                                                                                                                                                                                                                                                                                | 3.8                     |
| ASTM      C 131, “Resistance to Abrasion of Small Size Coarse Aggregate by Use of      the Los Angeles Machine,” 2001                                                                                                                                                                                                                                                                                                                                                                     | 3.8                     |
| ASTM      C 150, “Specification for Portland Cement,” 2002                                                                                                                                                                                                                                                                                                                                                                                                                                     | 3.8                     |
| ASTM      C 260, “Air Entraining Admixtures for Concrete,” 2001                                                                                                                                                                                                                                                                                                                                                                                                                                | 3.8                     |
| ASTM      C 311, “Sampling and Testing Fly Ash or Natural Pozzolans for Use as      Mineral Admixture in Portland Cement Concrete,” 2002                                                                                                                                                                                                                                                                                                                                                       | 3.8                     |
| ASTM      C 494, “Chemical Admixtures for Concrete,” 1999                                                                                                                                                                                                                                                                                                                                                                                                                                      | 3.8                     |
| ASTM      C 535, “Test Method for Resistance to Degradation of Large-Size Coarse      Aggregate by Abrasion and Impact in the Los Angeles Machine,”      2001                                                                                                                                                                                                                                                                                                                                  | 3.8                     |
| ASTM      C 618, “Fly Ash and Raw or Calcined Natural Pozzolans for Use in Portland      Cement Concrete,” 2001                                                                                                                                                                                                                                                                                                                                                                                | 3.8                     |
| ASTM      D 512, “Chloride Ion in Industrial Water,” 1999                                                                                                                                                                                                                                                                                                                                                                                                                                      | 3.8                     |
| ASTM      D 1888, "Particulate and Dissolved Matter in Industrial      Water."                                                                                                                                                                                                                                                                                                                                                                                                                             | 3.8                     |
| ASTM      E 142, “Methods for Controlling Quality of Radiographic Testing,”      1986                                                                                                                                                                                                                                                                                                                                                                                                          | 4.2                     |
| ASTM      E 165, “Practice for Liquid Penetrant Inspection Method,”    1995                                                                                                                                                                                                                                                                                                                                                                                                                    | 5.4                     |
| ASTM      E 185, “Standard Practice for Conducting Surveillance Tests for      Light-Water Cooled Nuclear Power Reactor Vessels,” 1982                                                                                                                                                                                                                                                                                                                                                         | 5.3                     |
| ASTM      E 741, “Standard Test Methods for Determining Air Change in a Single Zone      by Means of a Tracer Gas Dilution,” 2000                                                                                                                                                                                                                                                                                                                                                              | 6.4,      9.4           |
| AWWA      – American Water Works Association                                                                                                                                                                                                                                                                                                                                                                                                                                                         |                    |
| AWWA      D100, “Welded Steel Tanks for Water Storage,” 1984                                                                                                                                                                                                                                                                                                                                                                                                                                   | 3.2                     |
| AWS      – American Welding SocietyAWS      D1.1 Structural Welding Code – 2000 - SteelCovers      the design, welding and examination of welded structural steel 1/8" and      thicker. It allows for both pre-qualified and non prequalified welding      procedures.AWS D      1.4-98 Reinforcing Steel Welding      Code,                                                                                                                                                             | 3.8.3.2                 |
| CMAA      – Crane Manufacturers Association of America                                                                                                                                                                                                                                                                                                                                                                                                                                               |                    |
| CMAA      Specifications, “Specification for Electric Overhead Traveling Cranes,”      1999                                                                                                                                                                                                                                                                                                                                                                                                    | 9.1                     |
| FEMA      – Federal Emergency Management Agency                                                                                                                                                                                                                                                                                                                                                                                                                                                      |                    |
| FEMA      356, “Prestandard and Commentary for the Seismic Rehabilitation of      Buildings,” 2000                                                                                                                                                                                                                                                                                                                                                                                             | 3.7                     |
| IEEE      – Institute of Electrical and Electronics Engineers                                                                                                                                                                                                                                                                                                                                                                                                                                        |                    |
| IEEE      Standard 7-4.3.2, “IEEE Standard Criteria for Digital Computers in Safety      Systems of Nuclear Power Generating Stations,” 1993                                                                                                                                                                                                                                                                                                                                                   | 1A,      7.1            |
| IEEE      Standard 98, “IEEE Standard for the Preparation of Test Procedures for the      Thermal Evaluation of Solid Electrical Insulating Materials,”      1984                                                                                                                                                                                                                                                                                                                              | 3D                      |
| IEEE      Standard 100, “IEEE Standard Dictionary of Electrical and Electronic      Terms,” 1996                                                                                                                                                                                                                                                                                                                                                                                               | 3D                      |
| IEEE      Standard 141, “IEEE Recommended Practice for Electric Power Distribution      for Industrial Plants,” (IEEE Red Book), 1993                                                                                                                                                                                                                                                                                                                                                          | 8.3                     |
| IEEE      Standard 242, “IEEE Recommended Practice for Protection and Coordination      of Industrial and Commercial Power Systems” (IEEE Buff Book),      1986                                                                                                                                                                                                                                                                                                                                | 8.3                     |
| IEEE      Standard 279, “IEEE Standard Criteria for Protection Systems for Nuclear      Power Generating Stations,” 1971                                                                                                                                                                                                                                                                                                                                                                       | 1A                      |
| IEEE      Standard 281, “IEEE Standard Service Conditions for Power System      Communication Equipment,” 1984                                                                                                                                                                                                                                                                                                                                                                                 | 9.5                     |
| IEEE      Standard 308, “IEEE Standard Criteria for Class 1E Power Systems for      Nuclear Power Generating Stations,” 1991                                                                                                                                                                                                                                                                                                                                                                   | 1A,      8.1, 8.3       |
| IEEE      Standard 317, “IEEE Standard for Electric Penetrations Assemblies in      Containment Structures for Nuclear Power Generating Stations,”      1983                                                                                                                                                                                                                                                                                                                                   | 1.9,      1A, 8.1, 8.3  |
| IEEE      Standard 323, “IEEE Standard for Qualifying Class 1E Equipment for Nuclear      Power Generating Stations,” 1974                                                                                                                                                                                                                                                                                                                                                                     | 1.9,      1A, 3.2, 8.1  |
| IEEE      Standard 338, “IEEE Standard Criteria for the Periodic Surveillance      Testing of Nuclear Power Generating Stations Safety Systems,”      1987                                                                                                                                                                                                                                                                                                                                     | 1.9,      1A, 8.1       |
| IEEE      Standard 344, “IEEE Recommended Practice for Seismic Qualification of      Class 1E Equipment for Nuclear Power Generating Stations,”      1987                                                                                                                                                                                                                                                                                                                                      | 3.2,      3F, 8.1       |
| IEEE      Standard 379, “IEEE Standard Application of the Single-Failure Criterion      to Nuclear Power Generating Station Safety Systems,” 2000                                                                                                                                                                                                                                                                                                                                              | 1A,      8.1            |
| IEEE      Standard 381, “IEEE Standard Criteria for Type Test of Class 1E Modules      used in Nuclear Power Generating Stations,” 1977                                                                                                                                                                                                                                                                                                                                                        | 3D                      |
| IEEE      Standard 382, “IEEE Standard for Qualification of Actuators for      Power-Operated Valve Assemblies with Safety-Related Functions for Nuclear      Power Plants,” 1996                                                                                                                                                                                                                                                                                                              | 1A,      8.1            |
| IEEE      Standard 383, “IEEE Standard for Type Test of Class 1E Electric Cables,      Field Splices, and Connections for Nuclear Power Generating Stations,”      1974                                                                                                                                                                                                                                                                                                                        | 8.1,      9.5           |
| IEEE      Standard 384, “IEEE Standard Criteria for Independence of Class 1E      Equipment and Circuits,” 1981                                                                                                                                                                                                                                                                                                                                                                                | 1A,      1.9, 8.1, 8.3  |
| IEEE      Standard 420, “IEEE Standard for the Design and Qualification of Class 1E      Control Boards, Panels, and Racks Used in Nuclear Power Generating      Stations,” 1982                                                                                                                                                                                                                                                                                                               | 7.1                     |
| IEEE      Standard 422, “Guide for the Design and Installation of Cable Systems in      Power Generating Stations,” 1986                                                                                                                                                                                                                                                                                                                                                                       | 8.3                     |
| IEEE      Standard 450, “IEEE Recommended Practice for Maintenance, Testing, and      Replacement of Vented Lead-Acid Batteries for Stationary Applications,”      1995                                                                                                                                                                                                                                                                                                                        | 8.1,      8.3           |
| IEEE      Standard 484, “IEEE Recommended Practice for Installation Design and      Installation of Vented Lead-Acid Batteries for Stationary Applications,”      1996                                                                                                                                                                                                                                                                                                                         | 1A,      8.1            |
| IEEE      Standard 485, “IEEE Recommended Practice for Sizing Lead-Acid Batteries      for Stationary Applications,” 1997                                                                                                                                                                                                                                                                                                                                                                      | 8.3                     |
| IEEE      Standard 494, “IEEE Standard Method for Identification of Documents      Related to Class 1E Equipment and Systems for Nuclear Power Generating      Stations,” 1974                                                                                                                                                                                                                                                                                                                 | 3D                      |
| IEEE      Standard 535, “IEEE Standard for Qualification of Class 1E Lead Storage      Batteries for Nuclear Power Generating Stations,” 1986                                                                                                                                                                                                                                                                                                                                                  | 1A                      |
| IEEE      Standard 572, “IEEE Standard for Qualification of Class 1E Connection      Assemblies for Nuclear Power Generating Stations,” 1985                                                                                                                                                                                                                                                                                                                                                   | 3D                      |
| IEEE      Standard 603, “IEEE Standard Criteria for Safety Systems for Nuclear Power      Generating Stations,” 1991                                                                                                                                                                                                                                                                                                                                                                           | 1A,      7.1            |
| IEEE      Standard 627, “IEEE Standard for Design Qualification of Safety System      Equipment Used in Nuclear Power Generating Stations,” 1980                                                                                                                                                                                                                                                                                                                                               | 7.1                     |
| IEEE      Standard 649, “IEEE Standard for Qualifying Class 1E Motor Control Centers      for Nuclear Power Generating Stations,” 1991                                                                                                                                                                                                                                                                                                                                                         | 3D                      |
| IEEE      Standard 650, “IEEE Standard for Qualification of Class 1E Static Battery      Chargers and Inverters for Nuclear Power Generating Stations,”      1990                                                                                                                                                                                                                                                                                                                              | 3D                      |
| IEEE      Standard 665, “IEEE Guide for Generating Station Grounding,”      1995                                                                                                                                                                                                                                                                                                                                                                                                               | 8.3                     |
| IEEE      Standard 741, “IEEE Standard Criteria for the Protection of Class 1E Power      Systems and Equipment in Nuclear Power Generating Stations,”      1997                                                                                                                                                                                                                                                                                                                               | 1A,      8.1, 8.3       |
| IEEE      Standard 828, “IEEE Standard for Software Configuration Management Plans,”      1990                                                                                                                                                                                                                                                                                                                                                                                                 | 7.1                     |
| IEEE      Standard 829, “IEEE Standard for Software Test Configuration,”      1983                                                                                                                                                                                                                                                                                                                                                                                                             | 7.1                     |
| IEEE      Standard 830, “Recommended Practice for Software Requirements      Specifications,” 1993                                                                                                                                                                                                                                                                                                                                                                                             | 7.1                     |
| IEEE      Standard 946, “IEEE Recommended Practice for the Design of DC Auxiliary      Power Systems for Generating Stations,” 1992                                                                                                                                                                                                                                                                                                                                                            | 8.3                     |
| IEEE      Standard 1012, “IEEE Standard for Software Verification and Validation      Plans,” 1986                                                                                                                                                                                                                                                                                                                                                                                             | 7.1                     |
| IEEE      Std 1023-2004, “IEEE Recommended Practice for the Application of Human      Factors Engineering to Systems, Equipment and Facilities of Nuclear Power      Generating Stations and Other Nuclear Facilities.”                                                                                                                                                                                                                                                                        | 18.8                    |
| IEEE      Standard 1028, “IEEE Standard for Software Reviews and Audits,”      1988                                                                                                                                                                                                                                                                                                                                                                                                            | 7.1                     |
| IEEE      Standard 1042, “IEEE Guide to Software Configuration Management,”      1987                                                                                                                                                                                                                                                                                                                                                                                                          | 7.1                     |
| IEEE      Standard 1050, “IEEE Guide for Instrumentation and Control Equipment      Grounding in Generating Stations,” 1996                                                                                                                                                                                                                                                                                                                                                                    | 8.3,      7.1           |
| IEEE      Standard 1074, “Standard for Developing Software Life Cycle Processes,”      1995                                                                                                                                                                                                                                                                                                                                                                                                    | 7.1                     |
| IEEE      Standard 1202, “IEEE Standard for Flame Testing of Cables for Use in Cable      Tray in Industrial and Commercial Occupancies,” 1991                                                                                                                                                                                                                                                                                                                                                 | 8.1,      1A, 9.5       |
| IEEE      Std 1289-1998, “IEEE Guide for the Application of Human Factors      Engineering in the Design of Computer-Based Monitoring and Control      Displays for Nuclear Power Generating Stations.”                                                                                                                                                                                                                                                                                        | 18.8                    |
| IEEE      Standard C37.98, “IEEE Standard for Seismic Testing of Relays,”      1987                                                                                                                                                                                                                                                                                                                                                                                                            | 3D                      |
| ISA      – Instrumentation, Systems and Automation Society                                                                                                                                                                                                                                                                                                                                                                                                                                           |                    |
| ISA      S7.3, “Quality Standard for Instrument Air,” 1981                                                                                                                                                                                                                                                                                                                                                                                                                                     | 9.3                     |
| MIL      – Military Standards and Specifications                                                                                                                                                                                                                                                                                                                                                                                                                                                     |                    |
| MIL-HDBK-759C,      “Human Engineering Design Guidelines,” 1995                                                                                                                                                                                                                                                                                                                                                                                                                                | 6.4                     |
| MIL-STD      1472E, “Human Engineering,” 1996                                                                                                                                                                                                                                                                                                                                                                                                                                                  | 6.4                     |
| NEMA      – National Electrical Manufacturers Association                                                                                                                                                                                                                                                                                                                                                                                                                                            |                    |
| NEMA      MG-1, “Motors and Generators,” Revision 1, 1998                                                                                                                                                                                                                                                                                                                                                                                                                                      | 3.2                     |
| NEMA      Standard Publication No. VE 1-1998, Metallic Cable Tray      Systems                                                                                                                                                                                                                                                                                                                                                                                                                             | 3F                      |
| NFPA      – National Fire Protection Association                                                                                                                                                                                                                                                                                                                                                                                                                                                     |                    |
| NFPA      10, “Standard for Portable Fire Extinguishers,” 1998                                                                                                                                                                                                                                                                                                                                                                                                                                 | 9.5                     |
| NFPA      13, “Standard for the Installation of Sprinkler Systems,”    1999                                                                                                                                                                                                                                                                                                                                                                                                                    | 9.5                     |
| NFPA      14, “Standard for Installation of Standpipe, Private Hydrants, and Hose      Systems,” 2000                                                                                                                                                                                                                                                                                                                                                                                          | 9.5                     |
| NFPA      15, “Standard for Water Spray Fixed Systems for Fire Protection,”      2001                                                                                                                                                                                                                                                                                                                                                                                                          | 9.5                     |
| NFPA      20, “Standard for the Installation of Stationary Pumps for Fire      Protection,” 1999                                                                                                                                                                                                                                                                                                                                                                                               | 9.5                     |
| NFPA      22, “Standard for Water Tanks for Private Fire Protection,”      1998                                                                                                                                                                                                                                                                                                                                                                                                                | 9.5                     |
| NFPA      24, “Standard for Installation of Private Fire Service Mains and Fire      Protection,” 1995                                                                                                                                                                                                                                                                                                                                                                                         | 9.5                     |
| NFPA      30, “Flammable and Combustible Liquids Code,” 2000                                                                                                                                                                                                                                                                                                                                                                                                                                   | 9.5                     |
| NFPA      50A, “Standard for Gaseous Hydrogen Systems at Consumer Sites,”      1999                                                                                                                                                                                                                                                                                                                                                                                                            | 9.5                     |
| NFPA      50B, “Standard for Liquefied Hydrogen Systems at Consumer Sites,”      1999                                                                                                                                                                                                                                                                                                                                                                                                          | 9.5                     |
| NFPA      70, “National Electrical Code (NEC),” 1999                                                                                                                                                                                                                                                                                                                                                                                                                                           | 8.3,      9.5           |
| NFPA      72, “National Fire Alarm Code,” 1999                                                                                                                                                                                                                                                                                                                                                                                                                                                 | 9.5                     |
| NFPA      90A, “Installation of Air-Conditioning and Ventilation Systems,”      1999                                                                                                                                                                                                                                                                                                                                                                                                           | 9.4                     |
| NFPA      92A, “Recommended Practice for Smoke Control Systems,”2000                                                                                                                                                                                                                                                                                                                                                                                                                           | 9.4,      9A            |
| NFPA      780, “Standard for the Installation of Lighting Protection Systems,”      2000                                                                                                                                                                                                                                                                                                                                                                                                       | 8.3,      9.5           |
| NFPA      804, “Standard for Fire Protection for Advanced Light Water Reactor      Electric Generating Plants,” 2001                                                                                                                                                                                                                                                                                                                                                                           | 9.5                     |
| SMACNA      – Sheet Metal and Air Conditioning Contractors National      Association                                                                                                                                                                                                                                                                                                                                                                                                                 |                    |
| SMACNA,      “HVAC Duct Construction Standards - Metal and Flexible,” Second Edition      1995                                                                                                                                                                                                                                                                                                                                                                                                 | 3A,      9.4            |
| SMACNA,      “HVAC Systems – Testing, Adjusting, and Balancing,” 1993                                                                                                                                                                                                                                                                                                                                                                                                                    | 9.4                     |
| SMACNA,      “Rectangular Industrial Duct Construction Standards,” 1980                                                                                                                                                                                                                                                                                                                                                                                                                        | 9.4                     |
| SMACNA,      “HVAC Duct Construction Standards - Metal and Flexible,”    1985                                                                                                                                                                                                                                                                                                                                                                                                                  | 3.2                     |
| SMACNA,      “Round Industrial Duct Construction Standard,” 1999                                                                                                                                                                                                                                                                                                                                                                                                                               | 9.4                     |
| SMACNA,      “HVAC Duct Leakage Test Manual,” 1985                                                                                                                                                                                                                                                                                                                                                                                                                                             | 9.4                     |
| UBC      – Uniform Building Code                                                                                                                                                                                                                                                                                                                                                                                                                                                                     |                    |
| UBC,      “Uniform Building Code,” 1997                                                                                                                                                                                                                                                                                                                                                                                                                                                        | 3.2                     |
| UL      – Underwriters Laboratories, Inc.                                                                                                                                                                                                                                                                                                                                                                                                                                                            |                    |
| UL      555, “Safety Fire Dampers,” 1999                                                                                                                                                                                                                                                                                                                                                                                                                                                       | 9.4                     |
| UL      555S, “Leakage Rated Dampers for Use in Smoke Control Systems,”      1999                                                                                                                                                                                                                                                                                                                                                                                                              | 9.4                     |
| UL      586, “High-Efficiency, Particulate, Air-Filter Units,”1996                                                                                                                                                                                                                                                                                                                                                                                                                             | 9.4                     |
| UL      900, “Test Performance of Air-Filter Unit,” 1994                                                                                                                                                                                                                                                                                                                                                                                                                                       | 9.4                     |
| UL      1995, “Heating and Cooling Equipment,” 1995                                                                                                                                                                                                                                                                                                                                                                                                                                            | 9.4                     |
| UL      1996, “Electric Duct Heating,” 1996                                                                                                                                                                                                                                                                                                                                                                                                                                                    | 9.4                     |

| ASME      NQA-2 Quality Assurance Requirements for Nuclear Power Plants 1989      Edition, through NQA-1c-1992, Addenda                | None |
|----------------------------------------------------------------------------------------------------------------------------------------|------|
| American      Society for Nondestructive Testing SNT-TC-1A, “Recommended Practice for      Non-Destructive Testing 1992 Edition. | None |
| CP-189  Qualification      and Certification of Nondestructive Testing Personnel  1995      Edition                | None |

| Potential      Components to be Supplied | Supplier                                                  |
|------------------------------------------|-----------------------------------------------------------|
| Steam      Generators                    | Doosan      Heavy Industries & Construction Co., Ltd. |
| Reactor      Vessel                      | Doosan      Heavy Industries & Construction Co., Ltd. |
| Reactor      Vessel Head                 | Doosan      Heavy Industries & Construction Co., Ltd. |
| Main      Turbine and Generator          | Toshiba                                                   |
| Pressurizer                              | Ansaldo      Camozzi                                      |
| Reactor      Coolant Pumps               | Curtiss-Wright      Electro-Mechanical Division           |
| Control      Rod Drive Mechanisms        | Curtiss-Wright      Electro-Mechanical Division           |
| Reactor      Coolant Piping              | Tioga      Pipe Supply                                    |
| Core      Makeup Tanks                   | IHI      Corporation                                      |

|   | If      this Agreement (together with other contracts with Contractor) is in the      amount of $10,000.00 or more and not otherwise  exempt: |
|--------|-----------------------------------------------------------------------------------------------------------------------------------------------|

| 1.   | 41      C.F.R. § 60-1.4(a), Equal Opportunity Clause, 48 C.F.R. § 52.222-26; 48      C.F.R. § 52.222-21, Prohibition of Segregated  Facilities. |
|----------------|----------------------------------------------------------------------------------------------------------------------------------------------------------------|

| 2.   | 41      C.F.R. § 60-741.4, Section 503 of the Rehabilitation Act of 1973 and 41      C.F.R. § 60-741.5(a), Equal Opportunity for Workers with Disabilities; 48      C.F.R. § 52.222-36. |
|----------------|--------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| 1.   | 41      C.F.R. § 60-250.5(a), Equal Opportunity for Special Disabled Veterans,      Veterans of the Vietnam Era, Recently Separated Veterans, and Other      Protected Veterans; 48 C.F.R. §52.222-35. |
|----------------|------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

| 1. | 48      C.F.R. § 22.804-1, Affirmative Action Programs; 48 C.F.R. § 52.222-25,      Affirmative Action Compliance. |
|----|------------------------------------------------------------------------------------------------------------------------------|

| 1.   | 48      C.F.R. § 52.219-8, Utilization of Small Business  Concerns. |
|----------------|--------------------------------------------------------------------------|

| 2.   | 48      C.F.R. § 52.219-9, Small Business and Small Disadvantaged and Women-Owned      Small Business Subcontracting PlanClause. |
|----------------|---------------------------------------------------------------------------------------------------------------------------------------|

| 3.   | Contractor      shall provide Owner with an aggressive Commercial Plan that meets both the      spirit and intent of Title 48 of the C.F.R., while saving Owner some of      the administrative costs associated with the full implementation of a      Small Business Subcontracting Plan per 48 C.F.R. §    52.219.9. |
|----------------|------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

|   | To the extent      required by law, executive order or  regulation: |
|--------|---------------------------------------------------------------------|

| 1. | 29      C.F.R. Part 1625, Executive Order 11141 (Discrimination on the Basis of      Age), Public Law 90-202 (Age Discrimination in Employment Act of 1967) and      the Age Discrimination in EmploymentAct. |
|----|---------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|

|      | Agency      Limitation                                                                                                                                                                                                                                                                                                                                      | EPC      Contract Section Reference |
|-----------|-------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------------|-------------------------------------|
| (a)       | Agree      upon a definitive contract price                                                                                                                                                                                                                                                                                                            | N/A                                 |
| (b)       | Execute      the EPC Contract                                                                                                                                                                                                                                                                                                                          | N/A                                 |
| (c)       | Issue      a Full Notice to Proceed                                                                                                                                                                                                                                                                                                                    | 3.2(b)                              |
| (d)       | Terminate      Second Unit                                                                                                                                                                                                                                                                                                                             | 3.3(b)                              |
| (e)       | With      respect to any Major Subcontract under Section 3.7, Agent shall not (i)      participate in any claim, action or proceeding; (ii) cure any default;      (iii) consent to termination, assignment or modification; or (iv) assume      or enter into any Major Subcontract in the event of Contractor’s      bankruptcy or insolvency  | 3.7                                 |
| (f)  | Substantial      Completion                                                                                                                                                                                                                                                                                                                                 | 8.2                                 |
| (g)  | Approve      payment of Final Payment                                                                                                                                                                                                                                                                                                                       | 8.3                                 |
| (h)       | Approve      substitute form of security or lower bond amount for Stone & Webster      and/or Westinghouse                                                                                                                                                                                                                                         | 8.6(b)      and 8.6(c)              |
| (i)       | Agree      to any Change Order that increases the overall costs incurred under the      EPC Contract by      $1M or more, or along with all prior Change Orders issued under the EPC      extends the Project Schedule for 3 months or more beyond the Substantial      Completion Date.                                                          | 9.2,      9.4                       |
| (j)       | Suspend      the EPC Contract for Owner’s Convenience                                                                                                                                                                                                                                                                                            | 22.1                                |
| (k)       | Terminate      the EPC Contract for Cause                                                                                                                                                                                                                                                                                                              | 22.2                                |
| (l)       | Elect      to take over the Project upon Owner’s Termination for Cause                                                                                                                                                                                                                                                                           | 22.2(c)                             |
| (m)       | Terminate      the EPC Contract for Owner’s Convenience                                                                                                                                                                                                                                                                                          | 22.3                                |
| (n)       | Terminate      for failure to obtain regulatory approvals                                                                                                                                                                                                                                                                                              | 22.4                                |
| (o)       | File      a Claim, initiate the dispute resolution process, or initiate or defend a      lawsuit involving a third party in connection with the EPC      Contract                                                                                                                                                                                      | 27                                  |
| (p)       | Consent      to entry of any judgment or award in a disputed matter in connection with      the EPC Contract or enter into any settlement or compromise of a dispute      in connection with the EPC Contract                                                                                                                                          | N/A                                 |
| (q)       | Consent      to an assignment of the EPC Contract                                                                                                                                                                                                                                                                                                      | 29                                  |
| (r)       | Materially      amend, modify or supplement the EPC Contract                                                                                                                                                                                                                                                                                           | 31                                  |

|   |  |   |
|--------|--|--------|

|   |  |   |
|--------|--|--------|