6560-50-P

ENVIRONMENTAL PROTECTION AGENCY

40 CFR Part 63

[EPA-HQ-OAR-2002-0058; FRL- ]

RIN 2060-AG69

National Emission Standards for Hazardous Air Pollutants for 

Major Sources: Industrial, Commercial, and Institutional Boilers 

and Process Heaters

AGENCY: Environmental Protection Agency (EPA).

ACTION: Proposed rule.

SUMMARY: On September 13, 2004, under authority of section 112 

of the Clean Air Act, EPA promulgated national emission 

standards for hazardous air pollutants for new and existing 

industrial/commercial/institutional boilers and process heaters. 

On June 19, 2007, the United States Court of Appeals for the 

District of Columbia Circuit vacated and remanded the national 

emission standards for hazardous air pollutants for 

industrial/commercial/institutional boilers and process heaters.

In response to the court’s vacatur and remand, this action

would require all major sources to meet hazardous air pollutants

emissions standards reflecting the application of the maximum 

achievable control technology. The proposed rule would protect 
2

air quality and promote public health by reducing emissions of 

the HAP listed in section 112(b)(1) of the Clean Air Act.

DATES: Comments must be received on or before [INSERT DATE 45

DAYS AFTER PUBLICATION IN THE FEDERAL REGISTER]. Under the 

Paperwork Reduction Act, comments on the information collection 

provisions are best assured of having full effect if the Office 

of Management and Budget (OMB) receives a copy of your comments 

on or before [INSERT DATE 30 DAYS AFTER PUBLICATION IN THE 

FEDERAL REGISTER].

ADDRESSES: Submit your comments, identified by Docket ID No. 

EPA-HQ-OAR-2002-0058, by one of the following methods:

• http://www.regulations.gov. Follow the instructions 

for submitting comments.

• http://www.epa.gov/oar/docket.html. Follow the 

instructions for submitting comments on the EPA Air 

and Radiation Docket Web Site.

• E-mail: Comments may be sent by electronic mail (email) to a-and-r-docket@epa.gov, Attention Docket ID 

No. EPA-HQ-OAR-2002-0058.

• Fax

•

: Fax your comments to: (202) 566-9744, Docket ID 

No. EPA-HQ-OAR-2002-0058.

Mail: Send your comments to: EPA Docket Center

(EPA/DC), Environmental Protection Agency, Mailcode:
3

2822T, 1200 Pennsylvania Ave., NW, Washington, DC 

20460, Docket ID No. EPA-HQ-OAR-2002-0058. Please 

include a total of two copies. In addition, please 

mail a copy of your comments on the information 

collection provisions to the Office of Information and 

Regulatory Affairs, OMB, Attn: Desk Officer for EPA, 

725 17th St., NW, Washington, DC 20503. 

• Hand Delivery or Courier: Deliver your comments to: 

EPA Docket Center, EPA West, Room 3334, 1301 

Constitution Ave., NW, Washington, DC 20460. Such 

deliveries are only accepted during the Docket’s 

normal hours of operation (8:30 a.m. to 4:30 p.m., 

Monday through Friday, excluding legal holiday), and 

special arrangements should be made for deliveries of 

boxed information.

Instructions: All submissions must include agency name and 

docket number or Regulatory Information Number (RIN) for this 

rulemaking. All comments will be posted without change and may 

be made available online at http://www.regulations.gov, 

including any personal information provided, unless the comment 

includes information claimed to be confidential business 

information (CBI) or other information whose disclosure is 

restricted by statute. Do not submit information that you 
4

consider to be CBI or otherwise protected through 

http://www.regulations.gov or e-mail. The 

http://www.regulations.gov web site is an “anonymous access” 

system, which means EPA will not know your identity or contact 

information unless you provide it in the body of your comment. 

If you send an e-mail comment directly to EPA without going 

through http://www.regulations.gov, your e-mail address will be 

automatically captured and included as part of the comment that 

is placed in the public docket and made available on the 

Internet. If you submit an electronic comment, EPA recommends 

that you include your name and other contact information in the 

body of your comment and with any disk or CD-ROM you submit. If 

EPA cannot read your comment due to technical difficulties and 

cannot contact you for clarification, EPA may not be able to 

consider your comment. Electronic files should avoid the use of 

special characters, any form of encryption, and be free of any 

defects or viruses.

Docket: All documents in the docket are listed in the 

http://www.regulations.gov index. Although listed in the index, 

some information is not publicly available, e.g., CBI or other 

information whose disclosure is restricted by statute. Certain 

other material, such as copyrighted material, will be publicly 

available only in hard copy form. Publicly available docket 
5

materials are available either electronically in 

http://www.regulations.gov or in hard copy at the EPA Docket

Center, Room 3334, 1301 Constitution Ave., NW, Washington, DC. 

The Public Reading Room is open from 8:30 a.m. to 4:30 p.m., 

Monday through Friday, excluding legal holidays. The telephone 

number for the Public Reading Room is (202) 566-1744, and the 

telephone number for the Air Docket is (202) 566-1742.

FOR FURTHER INFORMATION CONTACT: Mr. Brian Shrager, Energy 

Strategies Group, Sector Policies and Programs Division, (D243-

01), Office of Air Quality Planning and Standards, U.S. 

Environmental Protection Agency, Research Triangle Park, North 

Carolina 27711; Telephone number: (919) 541-7689; Fax number 

(919) 541-5450; E-mail address: shrager.brian@epa.gov. 

SUPPLEMENTARY INFORMATION:

The information presented in this preamble is organized as 

follows:

I. General Information

A. Does this action apply to me?

B. What should I consider as I prepare my comments to EPA?

C. Where can I get a copy of this document?

D. When would a public hearing occur?

II. Background Information

A. What is the statutory authority for the proposed rule?

B. Summary of the Natural Resources Defense Council v. EPA

Decision

C. Summary of Other Related Court Decisions

D. EPA’s Response to the Vacatur

E. What is the relationship between the proposed rule and other 

combustion rules?
6

F. What are the health effects of pollutants emitted from 

industrial/commercial/institutional boilers and process heaters?

III. Summary of the Proposed Rule

A. What source categories are affected by the proposed rule?

B. What is the affected source? 

C. Does the proposed rule apply to me?

D. What emission limitations and work practice standards must I 

meet?

E. What are the startup, shutdown, and malfunction (SSM) 

requirements?

F. What are the testing and initial compliance requirements?

G. What are the continuous compliance requirements?

H. What are the notification, recordkeeping and reporting 

requirements?

I. Submission of Emissions Test Results to EPA

IV. Rationale for the Proposed Rule

A. How did EPA determine which sources would be regulated under 

the proposed rule?

B. How did EPA select the format for the proposed rule?

C. How did EPA determine the proposed emission limitations for 

existing units?

D. How did EPA determine the MACT floor for existing units?

E. How did EPA consider beyond-the-floor for existing units?

F. Should EPA consider different subcategories for solid fuel 

boilers and process heaters?

G. How did EPA determine the proposed emission limitations for 

new units?

H. How did EPA determine the MACT floor for new units?

I. How did EPA consider beyond-the-floor for new units?

J. What other compliance alternatives were considered?

K. How did we select the compliance requirements?

L. What alternative compliance provisions are being proposed?

M. How did EPA determine compliance times for the proposed 

rule?

N. How did EPA determine the required records and reports for 

this proposed rule?

O. How does the proposed rule affect permits?

P. Alternative Standard for Consideration

V. Impacts of the Proposed Rule

A. What are the air impacts?

B. What are the water and solid waste impacts?

C. What are the energy impacts?

D. What are the control costs?

E. What are the economic impacts?

F. What are the social costs and benefits of the proposed 

rule?
7

VI. Public Participation and Request for Comment

VII. Relationship of the Proposed Action to Section 112(c)(6) of 

the CAA

VIII. Statutory and Executive Order Reviews

A. Executive Order 12866, Regulatory Planning and Review

B. Executive Order 13132, Federalism

C. Executive Order 13175, Consultation and Coordination with 

Indian Tribal Governments

D. Executive Order 13045, Protection of Children from 

Environmental Health Risks and Safety Risks

E. Unfunded Mandates Reform Act of 1995

F. Regulatory Flexibility Act as Amended by the Small 

Business Regulatory Enforcement Fairness Act (RFA) of 1996 

SBREFA), 5 U.S.C. 601 et Seq.

G. Paperwork Reduction Act

H. National Technology Transfer and Advancement Act

I. Executive Order 13211, Actions Concerning Regulations That 

Significantly Affect Energy Supply, Distribution, or Use

J. Executive Order 12898: Federal Actions to Address 

Environmental Justice in Minority Populations and Low-Income 

Populations

I. General Information

A. Does this action apply to me? 

The regulated categories and entities potentially affected 

by the proposed standards include:

Category

NAICS 

code1

Examples of potentially 

regulated entities

Any industry 

using a 

boiler or

process heater 

as defined in 

the proposed 

rule

211 Extractors of crude petroleum 

and natural gas

321 Manufacturers of lumber and 

wood products

322 Pulp and paper mills

325 Chemical manufacturers
8

324 Petroleum refineries, and 

manufacturers of coal 

products

316, 

326,

339 

Manufacturers of rubber and 

miscellaneous plastic 

products

331 Steel works, blast furnaces

332 Electroplating, plating, 

polishing, anodizing, and 

coloring

336 Manufacturers of motor 

vehicle parts and accessories

221 Electric, gas, and sanitary 

services

622 Health services

611 Educational services

1 North American Industry Classification System.

This table is not intended to be exhaustive, but rather 

provides a guide for readers regarding entities likely to be 

affected by this action. To determine whether your facility, 

company, business, organization, etc., would be regulated by 

this action, you should examine the applicability criteria in 40 

CFR 63.7485 of subpart DDDDD (National Emission Standards for 

Hazardous Air Pollutants (NESHAP) for Industrial, Commercial, 

and Institution Boilers and Process Heaters). If you have any 

questions regarding the applicability of this action to a 

particular entity, consult either the air permitting authority 

for the entity or your EPA regional representative as listed in 

40 CFR 63.13 of subpart A (General Provisions).
9

B. What should I consider as I prepare my comments to EPA?

Do not submit information containing CBI to EPA through 

http://www.regulations.gov or e-mail. Send or deliver 

information identified as CBI only to the following address: 

Roberto Morales, OAQPS Document Control Officer (C404-02), 

Office of Air Quality Planning and Standards, U.S. Environmental 

Protection Agency, Research Triangle Park, North Carolina 27711, 

Attention: Docket ID EPA-HQ-OAR-2002-0058. Clearly mark the 

part or all of the information that you claim to be CBI. For 

CBI information in a disk or CD-ROM that you mail to EPA, mark 

the outside of the disk or CD-ROM as CBI and then identify 

electronically within the disk or CD-ROM the specific 

information that is claimed as CBI. In addition to one complete 

version of the comment that includes information claimed as CBI, 

a copy of the comment that does not contain the information 

claimed as CBI must be submitted for inclusion in the public 

docket. Information so marked will not be disclosed except in 

accordance with procedures set forth in 40 CFR part 2. 

C. Where can I get a copy of this document?

In addition to being available in the docket, an electronic 

copy of this proposed action will also be available on the 

Worldwide Web (WWW) through the Technology Transfer Network 

(TTN). Following signature, a copy of the proposed action will 
10

be posted on the TTN’s policy and guidance page for newly 

proposed or promulgated rules at the following address: 

http://www.epa.gov/ttn/oarpg/. The TTN provides information and 

technology exchange in various areas of air pollution control.

D. When would a public hearing occur?

If anyone contacts EPA requesting to speak at a public 

hearing concerning the proposed rule by [INSERT DATE 10 DAYS 

AFTER PUBLICATION IN THE FEDERAL REGISTER], we will hold a 

public hearing on [INSERT DATE 15 DAYS AFTER PUBLICATION IN THE 

FEDERAL REGISTER]. Persons interested in presenting oral 

testimony at the hearing, or inquiring as to whether a hearing 

will be held, should contact Ms. Pamela Garrett, Energy 

Strategies Group, at (919) 541-7966 at least 2 days in advance 

of the hearing. If a public hearing is held, it will be held at 

10 a.m. at the EPA’s Campus located at 109 T.W. Alexander Drive 

in Research Triangle Park, NC, or at an alternate site nearby.

II. Background Information

A. What is the statutory authority for this proposed rule?

Section 112(d) of the Clean Air Act (CAA) requires EPA to 

set emissions standards for hazardous air pollutants (HAP) 

emitted by major stationary sources based on the performance of 

the maximum achievable control technology (MACT). The MACT

standards for existing sources must be at least as stringent as 
11

the average emissions limitation achieved by the best performing 

12 percent of existing sources (for which the Administrator has

emissions information) or the best performing 5 sources for 

source categories with less than 30 sources (CAA section

112(d)(3)(A) and (B)). This level of minimum stringency is 

called the MACT floor. For new sources, MACT standards must be 

at least as stringent as the control level achieved in practice 

by the best controlled similar source (CAA section 112(d)(3)). 

EPA also must consider more stringent “beyond-the-floor” control 

options. When considering beyond-the-floor options, EPA must 

consider not only the maximum degree of reduction in emissions 

of HAP, but must take into account costs, energy, and nonair

environmental impacts when doing so.

CAA section 112(c)(6) requires EPA to list categories and 

subcategories of sources assuring that sources accounting for 

not less than 90 percent of the aggregate emissions of each such 

pollutant (alkylated lead compounds; polycyclic organic matter;

hexachlorobenzene; mercury; polychlorinated byphenyls; 2,3,7,8-

tetrachlorodibenzofurans; and 2,3,7,8-

tetrachloroidibenzo-p-dioxin) are subject to standards under 

subsection 112(d)(2) or (d)(4). Standards established under CAA 

section 112(d)(2) must reflect the performance of MACT. 

“Industrial Coal Combustion,” “Industrial Oil Combustion,” 
12

“Industrial Wood/Wood Residue Combustion,” “Commercial Coal 

Combustion,” “Commercial Oil Combustion,” and “Commercial 

Wood/Wood Residue Combustion” are listed as source categories

for regulation pursuant to CAA section 112(c)(6) due to 

emissions of polycyclic organic matter (POM) and mercury (63 FR 

17838, 17848, April 10, 1998). In the documentation for the 

112(c)(6) listing, the commercial fuel combustion categories 

included institutional fuel combustion (“1990 Emissions 

Inventory of Section 112(c)(6) Pollutants, Final Report,” April 

1998).

CAA section 129(a)(1)(A) requires EPA to establish specific

performance standards, including emission limitations, for 

“solid waste incineration units” generally, and, in particular, 

for “solid waste incineration units combusting commercial or

industrial waste” (section 129(a)(1)(D)). Section 129 defines 

“solid waste incineration unit” as “a distinct operating unit of 

any facility which combusts any solid waste material from

commercial or industrial establishments or the general public.”

Section 129(g)(1). Section 129 also provides that “solid waste”

shall have the meaning established by EPA pursuant to its

authority under the Resource Conservation and Recovery Act. 

Section 129(g)(6).
13

In Natural Resources Defense Council v. EPA, 489 F. 3d 

1250, 1257–61 (D.C. Cir. 2007), the court vacated the

Commercial and Industrial Solid Waste Incineration (CISWI) 

Definitions Rule, 70 FR 55568 (September 22, 2005), which EPA 

issued pursuant to CAA section 129(a)(1)(D). In that rule, EPA

defined the term “commercial or industrial solid waste 

incineration unit” to mean a combustion unit that combusts 

“commercial or industrial waste.” The rule defined “commercial

or industrial waste” to mean waste combusted at a unit that does 

not recover thermal energy from the combustion for a useful 

purpose. Under these definitions, only those units that

combusted commercial or industrial waste and were not designed 

to, or did not operate to, recover thermal energy from the 

combustion would be subject to section 129 standards. The 

District of Columbia Circuit (DC Circuit) rejected the 

definitions contained in the CISWI Definitions Rule and 

interpreted the term “solid waste incineration unit” in CAA 

section 129(g)(1) “to unambiguously include among the

incineration units subject to its standards any facility that 

combusts any commercial or industrial solid waste material at 

all — subject to the four statutory exceptions identified in 

[CAA section 129(g)(1).]” NRDC v. EPA, 489 F.3d 1250, 1257–58.
14

CAA section 129 covers any facility that combusts any solid 

waste; CAA section 112(g)(6) directs the Agency to the Resource

Conservation and Recovery Act (RCRA) in terms of the definition 

of solid waste. The Agency is in the process of defining solid 

waste for purposes of Subtitle D of RCRA. EPA initiated a 

rulemaking to define which secondary materials are “solid waste”

for purposes of subtitle D (nonhazardous waste) of RCRA when

burned in a combustion unit. (See Advance Notice of Proposed

Rulemaking (74 FR 41, January 2, 2009) soliciting comment on 

whether certain secondary materials used as alternative fuels or

ingredients are solid wastes within the meaning of Subtitle D of 

RCRA.) If a unit combusts solid waste, it is subject to CAA 

section 129 of the Act, unless it falls within one of the four 

specified exceptions in CAA section 129(g).

The solid waste definitional rulemaking under RCRA is being 

proposed in a parallel action and is relevant to this proceeding 

because some industrial, commercial, or institutional boilers 

and process heaters combust secondary materials as alternative 

fuels. If an industrial, commercial, or institutional boilers 

and process heaters combusts secondary materials that are solid 

waste under the proposed definitional rule, those units would be 

subject to section 129. The units subject to this rule include 

those 
15

industrial, commercial, or institutional boilers and process 

heaters that do not combust solid waste. EPA recognizes that it 

has imperfect information on the exact nature of the secondary 

materials which boilers and process heaters combust, including, 

for example, how much processing of such materials occurs, if 

any. We nevertheless used the information currently available 

to the Agency to determine which materials are solid waste and 

therefore subject to CAA section 129, which are not solid waste 

and therefore subject to CAA section 112.

B. Summary of the Natural Resources Defense Council v. EPA

Decision

On September 13, 2004, EPA issued the NESHAP for 

Industrial, Commercial, and Institutional Boilers and Process 

Heaters (40 CFR 55218) (the Boiler MACT). We identified 18 

subcategories of boilers and process heaters emitting four 

different types of HAPs. See 69 FR 55,223-24. EPA set out to 

establish the MACT floor for each subcategory emitting each HAP 

according to the effectiveness of various add-on technologies. 

(See 68 FR 1660, 1674, Jan. 13, 2003 (proposed rule).) Applying 

this methodology, EPA set 25 numerical emission standards. The 

2004 final rule established emission limitations for particulate 

matter (PM), as a surrogate for non-mercury HAP metals, mercury,

and hydrogen chloride (HCl), as a surrogate for acid gas HAP,
16

for existing large solid fuel-fired sources only. For the 

remaining 47 boiler subcategory/HAP emissions, EPA determined 

that the appropriate MACT floor was “no emissions reduction” 

because “the best-performing sources were not achieving 

emissions reductions through the use of an emission control 

system and there were no other appropriate methods by which 

boilers and process heaters could reduce HAP emissions.” (69 FR 

55,233.) Accordingly, we established no standards. In 

addition, we set risk-based standards, also known as healthbased compliance alternatives, as alternatives to the MACT-based 

standards for hydrogen chloride and manganese.

EPA issued emissions standards for CISWI units on December 

1, 2000, and as part of that rulemaking, defined the term 

“commercial and industrial waste” to mean solid waste combusted 

in an enclosed device using controlled flame combustion without 

energy recovery that is a distinct operating unit of any 

commercial or industrial facility. In response to a petition 

for reconsideration, EPA filed a motion for voluntary remand, 

which the court granted on September 6, 2001. On remand, EPA 

solicited comments on the CISWI Rule’s definitions of “solid 

waste,” “commercial and industrial waste” and “CISWI unit.” On 

September 22, 2005, EPA issued the CISWI Definitions Rule, which 

contained definitions that were substantively the same as those 
17

issued before reconsideration. In particular, the 2005 CISWI 

Definitions Rule defined “commercial or industrial waste” to 

include only waste that is combusted at a facility that cannot 

or does not use a process that recovers thermal energy from the 

combustion for a useful purpose.

EPA received separate petitions from environmental groups, 

industry, and municipalities seeking judicial review of the 

NESHAP for Industrial, Commercial, and Institutional Boilers and 

Process Heaters (Boiler MACT) as well as amendments to 

definitional terms in the Standards of Performance for New 

Stationary Sources and Emission Guidelines for Existing Sources: 

Commercial and Industrial Solid Waste Incineration Units (CISWI 

Definitions Rule), promulgated pursuant to CAA section 129. The 

environmental organizations challenged the CISWI Definitions 

Rule on the ground that its definition of “commercial or 

industrial waste” was inconsistent with the plain language of 

CAA section 129 and therefore impermissibly constricted the 

class of “solid waste incineration unit[s]” that were subject to 

the emission standards of the CISWI Rule. The environmental 

groups also challenged specific emission standards that EPA 

promulgated in the Boiler MACT and EPA’s methodology for setting 

them. The municipalities — the American Municipal Power-Ohio, 

Inc. and six of its members, the cities of Dover, Hamilton, 
18

Orrville, Painesville, Shelby and St. Mary’s, — challenged the 

Boiler MACT on the grounds that EPA failed to comply with the 

requirements of the Regulatory Flexibility Act (RFA) and that 

the standards as applied to small municipal utilities are 

unlawful.

As explained further below, the Court concluded that EPA’s 

definition of “commercial or industrial waste,” as incorporated 

in the definition of “commercial and industrial solid waste 

incineration unit” (CISWI unit), was inconsistent with the plain 

language of CAA section 129 and that the CISWI Definitions Rule 

must, therefore, be vacated. The Court also vacated the Boiler 

MACT, finding that the Boiler MACT must be substantially revised 

as a consequence of the vacatur and remand of the CISWI 

Definitions Rule.

In its decision, the Court agreed with the environmental 

petitioners that EPA’s definition of “commercial or industrial 

waste,” as incorporated in the definition of CISWI units, 

conflicted with the plain language of CAA section 129(g)(1). 

That provision defines “solid waste incineration unit” to mean 

“any facility which combusts any solid waste material” from 

certain types of establishments, with four specific exclusions. 

The Court stated that, based on the use of the term “any” and 

the specific exclusions for only certain types of facilities 
19

from the definition of “solid waste incineration unit,” CAA 

section 129 unambiguously includes among the incineration units 

subject to its standards any facility that combusts any 

commercial or industrial solid waste material at all — subject 

only to the four statutory exclusions. The Court held that the 

definitions EPA promulgated in the CISWI Definitions Rule 

constricted the plain language of CAA section 129(g)(1), because 

the CISWI Definitions Rule excluded from its universe operating 

units that combusted solid waste and were designed for or 

operating with energy recovery. 

Having determined that EPA’s definition of “commercial and 

industrial solid waste incineration unit” conflicts with the 

plain meaning of CAA section 129 and must, therefore, be 

vacated, the Court also vacated the Boiler MACT because it 

concluded that the Boiler MACT would need to be revised because 

the universe of boilers subject to its standards will be 

different once EPA revises the CISWI definitions rule consistent 

with the Court’s opinion. The Court did not address 

petitioners’ specific challenges to the Boiler MACT.

C. Summary of Other Related Court Decisions

In March 2007, the D.C. Circuit Court issued an opinion 

(Sierra Club v. EPA, 479 F. 3d 875 (DC Cir. 2007) (Brick
20

MACT)) vacating and remanding CAA section 112(d) MACT standards 

for the Brick and Structural Clay Ceramics source categories. 

Some key holdings in that case were:

• Floors for existing sources must reflect the average 

emission limitation achieved by the best-performing 12

percent of existing sources, not levels EPA considers to be 

achievable by all sources (479 F. 3d at 880–81);

• EPA cannot set floors of “no control.” The Court 

reiterated its prior holdings, including National Lime

Association, confirming that EPA must set floor standards 

for all HAP emitted by the major source, including those 

HAP that are not controlled by at-the-stack control devices 

(479 F. 3d at 883);

• EPA cannot ignore non-technology factors that reduce HAP 

emissions. Specifically, the Court held that “EPA’s

decision to base floors exclusively on technology even 

though non-technology factors affect emissions violates the

Act.” (479 F. 3d at 883)

Based on the Brick MACT decision, we believe a source’s 

performance resulting from the presence or absence of HAP in 

fuel materials must be accounted for in establishing floors; 

i.e., a low emitter due to low HAP fuel materials can still be a

best performer. In addition, the fact that a specific level of 
21

performance is unintended is not a legal basis for excluding the 

source’s performance from consideration. (National Lime Ass’n, 

233 F. 3d at 640.)

The Brick MACT decision also stated that EPA may account 

for variability in setting floors. However, the court found

that EPA erred in assessing variability because it relied on 

data from the worst performers to estimate best performers’

variability, and held that “EPA may not use emission levels of 

the worst performers to estimate variability of the best 

performers without a demonstrated relationship between the two.”

(479 F. 3d at 882.)

The majority opinion in the Brick MACT case does not 

address the possibility of subcategorization to address 

differences in the HAP content of raw materials. However, in 

his concurring opinion Judge Williams stated that EPA’s ability 

to create subcategories for sources of different classes, size, 

or type (CAA section 112 (d)(1)) may provide a means out of the

situation where the floor standards are achieved for some 

sources, but the same floors cannot be achieved for other

sources due to differences in local raw materials whose use is 

essential. (Id. At 884–85.9)

A second court opinion is also relevant to this proposal. 

In Sierra Club v. EPA, 551 F. 3d 1019 (D.C. Cir. 2008), the 
22

court vacated the portion of the regulations contained in the 

General Provisions which exempt major sources from MACT 

standards during periods of startup, shutdown and malfunction

(SSM). The regulations (in 40 CFR 63.6(f)(1) and 63.6(h)(1)) 

provided that sources need not comply with the relevant CAA 

section 112(d) standard during SSM events and instead must

“minimize emissions . . . to the greatest extent which is 

consistent with safety and good air pollution control

practices.” The vacated Boiler MACT did not contain specific

provisions covering operation during SSM operating modes; rather 

it referenced the now-vacated exemption in the General 

Provisions. As a result of the court decision, we are 

addressing SSM in this proposed rulemaking. Discussion of this

issue may be found later in this preamble.

D. EPA’s Response to the Vacatur

In response to the NRDC v. EPA mandate, we initiated an 

information collection effort entitled “Information Collection 

Effort for Facilities with Combustion Units.” This information 

collection was conducted by EPA’s Office of Air and Radiation 

pursuant to CAA section 114 to assist the Administrator in 

developing emissions standards for boilers/process heaters and 

CISWI units (collectively, “combustion units”) pursuant to CAA 
23

sections 112(d) and 129. CAA section 114(a) states, in pertinent 

part:

For the purpose of ...(iii) carrying out any provision of 

this Chapter...(1) the Administrator may require any person 

who owns or operates any emission source...to-. . .(D) sample 

such emissions (in accordance with such procedures or 

methods, at such locations, at such intervals, during such 

periods and in such manner as the Administrator shall 

prescribe); (E) keep records on control equipment parameters, 

production variables or other indirect data when direct 

monitoring of emissions is impractical.. .(G) provide such 

other information as the Administrator may reasonably 

require...

There were two components to the information collection. 

To obtain the information necessary to identify and categorize 

all combustion units potentially affected by the revised 

standards for boilers/process heaters and for CISWI units, the 

first component of the information collection effort solicited

information from all potentially affected combustion units in the 

format of an electronic survey. The survey was submitted to the 

following facilities: (1) all facilities that submitted an 

initial notification for the 2004 boiler MACT standard, (2) all 

facilities identified by States as being subject to the 2004 
24

boiler MACT standard, and (3) facilities that are classified as a 

major source in their Title V permit that have a boiler or 

process heater listed in their permit. The survey was also sent 

to units covered by the 2000 CISWI emissions standards (40 CFR 

part 60 subpart CCCC) and to facilities that have incineration 

units that were listed as exempt under the 2000 CISWI standard. 

Each facility was required to complete the survey for all 

combustion units located at the facility. The information 

requested for each combustion unit included the unit design, 

operation, air pollution control data, the fuels/materials 

burned, and available emissions test data, continuous emission 

monitoring (CEM) data, fuel/material analysis data, and 

permitted and regulatory emission limits.

The second component of the information collection request 

effort consisted of requiring the owners/operators of 169

boilers/process heaters to conduct emission testing for HAP and 

HAP surrogates. We first analyzed the results of the survey to 

determine if sufficient emissions data existed to develop 

emission standards under CAA sections 112(d) for all types of 

boilers/process heaters, all types of materials combusted, and 

all HAP to be regulated. If data were not sufficient, then we

selected pools of candidates to conduct emission testing. We

submitted a list of candidates to stakeholders, including state, 
25

industry, and environmental stakeholders, who had an opportunity 

to comment on the technical feasibility, the least-cost impact 

of the testing program, and the appropriateness of the testing 

being requested. We then made a selection of test sites after 

taking into account stakeholder comments. The sites selected 

were required to conduct an outlet stack test, consisting of 

three runs, in accordance with EPA-approved protocols, for all 

of the following pollutants: PM (filterable, condensable, and 

PM2.5), dioxins/furans (D/F), hydrogen chloride/hydrogen fluoride, 

mercury, metals (including antimony, arsenic, beryllium, 

cadmium, chromium, cobalt, lead, manganese, nickel, phosphorus, 

and selenium), carbon monoxide (CO), total hydrocarbons (THC), 

formaldehyde, oxides of nitrogen (NOx), and sulfur dioxide 

(SO2). Six facilities (two coal-fired, two biomass-fired, and 

two gas-fired boilers) were required to collect CEM data over 30 

operating days using mobile CEM devices for CO, THC, and NOx. 

The owner/operator of each selected combustion unit was also 

required to collect and analyze, in accordance with acceptable 

procedures, the material(s) fed to the combustion unit during 

each stack test. The results of the stack tests and the 

analyses of materials combusted were required to be submitted to 

the Agency.
26

When we compared information on boilers and process heaters

from facilities submitting initial notifications to comply with 

the vacated 2004 Boiler MACT to the information gathering effort 

conducted for the 2004 Boiler MACT, a large disparity was 

identified in the number of potentially affected units at major 

sources of HAP. Since the last combustion unit data gathering 

effort in 1996, many sources have shut down, others have selected 

to operate with a permit limit on their HAP emissions in order to 

avoid being subject to the Boiler MACT (i.e., synthetic area 

source), and some units have switched out older solid fuel units 

for newer equipment due to increased insurance and maintenance 

costs. 

Based on the definition of solid waste as set forth in a 

parallel proposed action, we revised the population of combustion 

units subject to CAA section 129 (because they combust solid 

waste) and the population of boilers and process heaters subject 

to CAA section 112 (because they do not combust solid waste). We 

then used the new data to develop a revised NESHAP for boilers and 

process heaters under CAA section 112 and revised standards for 

incineration units covered by CAA section 129. Specifically, 

the data provide the Agency with updated information on the number 

of potentially affected units, available emission test data, and 

fuel/material analysis data to address variability. We are using 
27

all of the information before the Administrator to calculate the 

MACT floors, set emission limits, and evaluate the emission 

impacts of various regulatory options for these revised 

rulemakings. 

E. What is the relationship between this proposed rule and 

other combustion rules?

The proposed rule regulates source categories covering 

industrial boilers, institutional boilers, commercial boilers, 

and process heaters. These source categories potentially 

include combustion units that are already regulated by other 

MACT standards. Therefore, we are excluding from this proposed 

rule any boiler or process heater that is subject to regulation 

under other MACT standards.

In 1986, EPA had codified new source performance standards 

(NSPS) for industrial boilers (40 CFR part 60, subparts Db and 

Dc) and revised portions of those standards in 1999 and 2006. 

The NSPS regulates emissions of PM, SO2, and NOx from boilers 

constructed after June 19, 1984. Sources subject to the NSPS 

will be subject to the final CAA section 112(d) standards for 

boilers and process heaters because it regulates sources of HAP

while the NSPS do not. However, in developing the proposed 

rule, we considered the monitoring requirements, testing 
28

requirements, and recordkeeping requirements of the NSPS to 

avoid duplicating requirements.

This proposed rule addresses the combustion of non-solid 

waste materials in boilers and process heaters. If an owner or 

operator of an affected source subject to these proposed 

standards were to start combusting a solid waste (as defined by 

the Administrator under RCRA), the affected source would cease 

to be subject to this action and would instead be subject to 

regulation under CAA section 129. A rulemaking under CAA 

section 129 is being proposed in a parallel action and is 

relevant to this action because it would apply to boilers and 

process heaters located at a major source that combust any solid 

waste. EPA is taking comment on whether a boiler or process 

heater could then opt back into regulation under this proposed 

rule by taking a federally enforceable restriction precluding

the future combustion of any solid waste material.

F. What are the health effects of pollutants emitted from 

industrial/commercial/institutional boilers and process heaters?

This proposed rule protects air quality and promotes the 

public health by reducing emissions of some of the HAP listed in 

CAA section 112(b)(1). As noted above, emissions data collected 

during development of the proposed rule show that hydrogen 

chloride emissions represent the predominant HAP emitted by 
29

industrial, commercial, and industrial (ICI) boilers, accounting 

for 84 percent of the total HAP emissions. ICI boilers and 

process heaters also emit lesser amounts of hydrogen fluoride, 

accounting for about 5 percent of total HAP emissions, and 

metals (arsenic, cadmium, chromium, mercury, manganese, nickel, 

and lead) accounting for about 0.3 percent of total HAP 

emissions. Organic HAP (formaldehyde, POM, acetaldehyde, 

benzene) account for about 11 percent of total HAP emissions. 

Exposure to these HAP is associated with a variety of adverse 

health effects. These adverse health effects include chronic 

health disorders (e.g., irritation of the lung, skin, and mucus 

membranes, effects on the central nervous system, and damage to 

the kidneys), and acute health disorders (e.g., lung irritation 

and congestion, alimentary effects such as nausea and vomiting, 

and effects on the kidney and central nervous system). We have 

classified two of the HAP as human carcinogens (arsenic and 

chromium VI) and four as probable human carcinogens (cadmium, 

lead, dioxins/furans, and nickel). We do not know the extent to 

which the adverse health effects described above occur in the 

populations surrounding these facilities. However, to the 

extent the adverse effects do occur, this proposed rule would 

reduce emissions and subsequent exposures.

III. Summary of this Proposed Rule
30

This section summarizes the requirements proposed in 

today’s action. Section IV below provides our rationale for the 

proposed requirements.

A. What source categories are affected by this proposed rule?

This proposed rule affects industrial boilers, 

institutional boilers, commercial boilers, and process heaters. 

In this proposed rule, process heaters are defined as units in 

which the combustion gases do not directly come into contact 

with process material or gases in the combustion chamber (e.g., 

indirect fired). Boiler means an enclosed device using 

controlled flame combustion and having the primary purpose of 

recovering thermal energy in the form of steam or hot water. 

B. What is the affected source? 

The affected source is: (1) the collection of all existing 

industrial, commercial, or institutional boilers or process 

heaters within a subcategory located at a major facility or (2) 

each new or reconstructed industrial, commercial, or 

institutional boiler or process heater located at a major 

facility that do not combust solid waste, as that term is 

defined by the Administrator under RCRA.

The affected source does not include boilers and process 

heaters that are subject to another standard under 40 CFR part 

63 or a standard established under CAA section 129.
31

C. Does this proposed rule apply to me?

This proposed rule applies to you if you own or operate a 

boiler or process heater at a major source meeting the 

requirements discussed previously in this preamble. A major 

source of HAP emissions is any stationary source or group of 

stationary sources located within a contiguous area and under 

common control that emits or has the potential to emit 

considering controls 10 tons per year or more of any HAP or 25 

tons per year or more of any combination of HAP.

D. What emission limitations and work practice standards must I 

meet?

We are proposing the emission limits presented in Table 1 

of this preamble. Emission limits were developed for new and 

existing sources for eleven subcategories, which we developed 

based on unit design. 

We are proposing that if your new or existing boiler or 

process heater burns more than 10 percent coal on a heat input1

 

1 Heat input means heat derived from combustion of fuel in a boiler or process heater and does not include the heat 

derived from preheated combustion air, recirculated flue gases or exhaust gases from other sources (such as 

stationary gas turbines, internal combustion engines, and kilns.

basis on an annual average, the unit is in one of the coal

subcategories. If your new or existing boiler or process heater 

burns more than 10 percent biomass, on a heat input basis on an 

annual average, and less than 10 percent coal, on a heat input 

basis on an annual average, we are proposing that the unit is in 
32

one of the biomass subcategories. If your new or existing 

boiler or process heater burns a liquid fuel (such as distillate 

oil, residual oil), or a liquid fuel in combination with a 

gaseous fuel, we are proposing that the unit is in one of the 

liquid subcategories. If your new or existing boiler or process 

heater burns gaseous fuel and less than 10 percent, on a heat 

input basis on an annual average, of liquid or solid fuel, we 

are proposing that the unit is in one of the gas subcategories. 

Table 1. EMISSION LIMITS FOR BOILERS AND PROCESS HEATERS

(pounds per million British thermal units)

Subcategor

y

Particula

te Matter 

(PM)

Hydrogen 

Chloride 

(HCl)

Mercury

(Hg)

Carbon 

Monoxide(CO)

(ppm

@3%oxygen)

Dioxins/

Furans

(Total 

TEQ)

(ng/dscm)

Existing –

Coal 

Stoker 

0.02 0.008 0.000003 50 0.003

Existing -

Coal 

Fluidized 

Bed

0.02 0.008 0.000003 30 0.002

Existing –

Pulverized 

Coal

0.02 0.008 0.000003 90 0.004

Existing –

Biomass 

Stoker 

0.02 0.006 0.0000009 560 0.004

Existing -

Biomass 

Fluidized 

Bed

0.02 0.006 0.0000009 250 0.02

Existing –

Biomass 

Suspension 

Burner/Dut

0.02 0.006 0.0000009 1010 0.03
33

ch Oven

Existing –

Biomass 

Fuel Cells

0.02 0.006 0.0000009 270 0.02

Existing -

Liquid

0.004 0.0004 0.000004 1 0.002

Existing –

Gas (Other 

Process 

Gases)

0.05 0.000003 0.0000002 1 0.009

New –Coal 

Stoker 

0.001 0.00006 0.000002 7 0.003

New - Coal 

Fluidized 

Bed

0.001 0.00006 0.000002 30 0.00003

New –

Pulverized 

Coal

0.001 0.00006 0.000002 90 0.002

New –

Biomass 

Stoker 

0.008 0.004 0.0000002 560 0.00005

New -

Biomass 

Fluidized 

Bed

0.008 0.004 0.0000002 40 0.007

New –

Biomass 

Suspension 

Burner/Dut

ch Oven

0.008 0.004 0.0000002 1010 0.03

New –

Biomass 

Fuel Cells

0.008 0.004 0.0000002 270 0.0005

New –

Liquid

0.002 0.0004 0.0000003 1 0.002

New – Gas 

(Other 

Process 

Gases)

0.003 0.000003 0.0000002 1 0.009

The proposed emission limits in the above table apply only 

to existing boilers and process heaters that have a designed 

heat input capacity of 10 million British thermal units (Btu) 
34

per hour or greater. Pursuant to CAA section 112(h), we are 

proposing a work practice standard for two particular classes of 

boilers and process heaters: existing units that have a designed

heat input capacity of less than 10 million Btu per hour and new 

and existing units in the Gas 1 (natural gas/refinery gas) 

subcategory and in the metal process furnaces subcategory. The 

work practice standard being proposed for these boilers and 

process heaters would require the implementation of a tune-up 

program as described in section III.F of this preamble.

We are also proposing a beyond-the-floor standard for all 

existing major source facilities having affected boilers or 

process heaters that would require the performance of an onetime energy assessment, as described in section III.F of this 

preamble, by qualified personnel, on the affected boilers and 

facility to identify any cost-effective energy conservation 

measures.

E. What are the startup, shutdown, and malfunction (SSM) 

requirements?

The United States Court of Appeals for the District of 

Columbia Circuit vacated two provisions in EPA’s CAA Section 112 

regulations governing the emissions of HAP during periods of 

SSM. Sierra Club v. EPA, 551 F.3d 1019 (D.C. Cir. 2008). 

Specifically, the Court vacated the SSM exemption contained in 
35

40 CFR 63.6(f)(1) and 40 CFR 63.6(h)(1), that are part of a 

regulation, commonly referred to as the “General Provisions 

Rule,” that EPA promulgated under section 112 of the CAA. When 

incorporated into CAA Section 112(d) regulations for specific 

source categories, these two provisions exempt sources from the 

requirement to comply with the otherwise applicable CAA section 

112(d) emission standard during periods of SSM.

In light of Sierra Club v. EPA, the proposed emission 

standards summarized in section IV.D of this preamble apply at 

all times. We are not proposing a separate emission standard 

for the source categories at issue here that applies during 

periods of startup and shutdown. We have evaluated whether it 

is appropriate to have the same standards apply during startup 

and shutdown as applied to normal operations. The standards 

that we are proposing are daily or monthly averages based upon 

emission data which include periods of startup and shutdown. 

Boilers do not normally startup and shutdown more than once per 

day. Thus, we are not establishing a separate emission standard 

for these periods because startup and shutdown are part of their 

normal operations and, therefore, are already addressed by the 

standards.

Periods of startup, normal operations, and shutdown are all 

predictable and routine aspects of a source’s operations. 
36

However, by contrast, malfunction is defined as a “sudden, 

infrequent, and not reasonably preventable failure of air 

pollution control and monitoring equipment, process equipment or 

a process to operate in a normal or usual manner * * * ’’(40 CFR 

63.2). EPA has determined that malfunctions should not be 

viewed as a distinct operating mode and, therefore, any 

emissions that occur at such times do not need to be factored 

into development of CAA section 112(d) standards, which, once 

promulgated, apply at all times. For example, we note that 

Section 112 uses the concept of “best performing” sources in 

defining MACT, the level of stringency that major source 

standards must meet. It is reasonable to interpret section 

112(d) as not requiring EPA to account for malfunctions in 

setting emissions standards. Applying the concept of “best 

performing” to a source that is malfunctioning presents 

difficulties. The goal of best performing sources is to operate 

in such a way as to avoid malfunctions of their units. 

Moreover, even if malfunctions were considered a distinct 

operating mode, we believe it would be impracticable to take 

malfunctions into account in setting CAA section 112(d) 

standards for boilers and process heaters. As noted above, by 

definition, malfunctions are sudden and unexpected events and it 

would be difficult to set a standard that takes into account the 
37

myriad different types of malfunctions that can occur across all 

sources. Moreover, malfunctions can vary in frequency, degree, 

and duration, further complicating standard setting.

For a source that fails to comply with the applicable 

Section 112(d) standards during malfunction events, EPA will 

determine an appropriate response based on, among other things, 

the good faith efforts of the source to minimize emissions 

during malfunction periods, including preventative and

corrective actions, as well as root cause analyses to ascertain 

and rectify excess emissions. EPA would also consider whether 

the source's failure to comply with the CAA section 112(d) 

standard was, in fact, “sudden, infrequent, not reasonably 

preventable” and was not instead “caused in part by poor 

maintenance or careless operation.” 40 C.F.R. § 63.2 

(definition of malfunction).

F. What are the testing and initial compliance requirements?

We are proposing that the owner or operator of a new or 

existing boiler or process heater must conduct performance tests 

to demonstrate compliance with all applicable emission limits. 

Affected units would be required to conduct the following 

compliance tests where applicable: 

(1) Conduct initial and annual stack tests to determine 

compliance with the PM emission limits using EPA Method 5 or 17.
38

(2) Conduct initial and annual stack tests to determine 

compliance with the mercury emission limits using EPA method 29 

or ASTM-D6784-02 (Ontario Hydro Method).

(3) Conduct initial and annual stack tests to determine 

compliance with the HCl emission limits using EPA Method 26A or 

EPA Method 26 (if no entrained water droplets in the sample).

(4) Use EPA Method 19 to convert measured concentration 

values to pound per million Btu values.

(5) Conduct initial and annual test to determine 

compliance with the CO emission limits using either EPA Method 

10 or a CO CEMS.

(6) Conduct initial and annual test to determine 

compliance with the D/F emission limits using EPA Method 23.

As part of the initial compliance demonstration, we are 

proposing that you monitor specified operating parameters during 

the initial performance tests that you would conduct to 

demonstrate compliance with the PM, mercury, D/F, and HCl 

emission limits. You would calculate the average parameter 

values measured during each test run over the three run

performance test. The average of the three average values 

(depending on the parameter measured) for each applicable 

parameter would establish the site-specific operating limit. 

The applicable operating parameters for which operating limits 
39

would be required to be established are based on the emissions 

limits applicable to your unit as well as the types of add-on 

controls on the unit. The following is a summary of the 

operating limits that we are proposing to be established for the 

various types of the following units:

(1) For boilers and process heaters without wet or dry 

scrubbers that must comply with an HCl emission limit, you must 

measure the average chlorine content level in the input fuel(s) 

during the HCl performance test. This is your maximum chlorine 

input operating limit. 

(2) For boilers and process heaters with wet scrubbers, 

you must measure pressure drop and liquid flow rate of the 

scrubber during the performance test, and calculate the average 

value for each test run. The average of the three test run 

averages establishes your minimum site-specific pressure drop 

and liquid flow rate operating levels. If different average 

parameter levels are measured during the mercury, PM and HCl 

tests, the highest of the average values becomes your sitespecific operating limit. If you are complying with an HCl 

emission limit, you must measure pH of the scrubber effluent 

during the performance test for HCl and determine the average 

for each test run and the average value for the performance 

test. This establishes your minimum pH operating limit.
40

(3) For boilers and process heaters with sorbent 

injection, you would be required to measure the sorbent 

injection rate during the performance tests for HCl, mercury,

and D/F and calculate the average for each test run. The 

average of the three test run averages established during the 

performance tests would be your site-specific minimum sorbent 

injection rate operating limit. If different sorbents and/or 

injection rates are measured during the mercury, HCl, and D/F 

tests, the highest of the average values becomes your sitespecific operating limit. 

(4) For boilers and process heaters with fabric filters in 

combination with wet scrubbers, you must measure the pH, 

pressure drop, and liquid flowrate of the wet scrubber during 

the performance test and calculate the average value for each 

test run. The minimum test run average establishes your sitespecific pH, pressure drop, and liquid flowrate operating limits 

for the wet scrubber. Furthermore, the fabric filter must be 

operated such that the bag leak detection system alarm does not 

sound more than 5 percent of the operating time during any 6-

month period unless a CEMS is installed to measure PM. 

(5) For boilers and process heaters with electrostatic 

precipitators (ESP) in combination with wet scrubbers, you must 

measure the pH, pressure drop, and liquid flow rate of the wet 
41

scrubber during the HCl performance test and you must measure 

the voltage and current of the ESP collection fields during the 

mercury and PM performance test. You would then be required to 

calculate the average value of these parameters for each test 

run. The average of the three test run averages would establish 

your site-specific minimum pH, pressure drop, and liquid 

flowrate operating limit for the wet scrubber and the minimum 

voltage and current operating limits for the ESP.

(6) For boilers and process heaters that choose to 

demonstrate compliance with the mercury emission limit on the 

basis of fuel analysis and have no add-on controls or add-on 

controls for which you do not want to take credit for any 

emission reduction of mercury, you would be required to measure 

the mercury content of the inlet fuel that was burned during the 

mercury performance test. This value is your maximum fuel inlet 

mercury operating limit. 

(7) For boilers and process heaters that choose to 

demonstrate compliance with the HCl emission limit on the basis 

of fuel analysis and have no add-on controls or add-on controls 

for which you do not want to take credit for any emission 

reduction of HCl, you would be required to measure the chlorine 

content of the inlet fuel that was burned during the HCl 
42

performance test. This value is your maximum fuel inlet 

chlorine operating limit. 

These proposed operating limits would not apply to owners 

or operators of boilers or process heaters having a heat input 

capacity of less than 10 million Btu per hour (MMBtu/h) or which 

combust natural gas or refinery gas. Instead, we are proposing 

that owners or operators of such boilers and process heaters

submit to the delegated authority or EPA, as appropriate, if 

requested, documentation that a tune-up meeting the requirements 

of the proposed rule was conducted. We are proposing that, to 

comply with the work practice standard, a tune-up procedure 

include the following:

(1) Inspect the burner, and clean or replace any 

components of the burner as necessary,

(2) Inspect the flame pattern and make any adjustments to 

the burner necessary to optimize the flame pattern consistent 

with the manufacturer’s specifications,

(3) Inspect the system controlling the air-to-fuel ratio, 

and ensure that it is correctly calibrated and functioning 

properly,

(4) Minimize total emissions of CO consistent with the 

manufacturer’s specifications,
43

(5) Measure the concentration in the effluent stream of CO 

in ppmvd, before and after the adjustments are made,

(6) Submit an annual report containing the concentrations 

of CO in the effluent stream in ppmvd, and oxygen in percent dry 

basis, measured before and after the adjustments of the boiler,

a description of any corrective actions taken as a part of the 

combustion adjustment, and the type and amount of fuel used over 

the 12 months prior to the annual adjustment. 

Further, all owners or operators of major source facilities 

having boilers and process heaters subject to this rule would be 

required to submit to the delegated authority or EPA, as 

appropriate, documentation that an energy assessment was 

performed, by qualified personnel, and the cost-effective energy 

conservation measures indentified. The procedures for an energy 

assessment are:

(1) Conduct a visual inspection of the boiler system.

(2) Establish operating characteristics of the facility, 

energy system specifications, operating and maintenance 

procedures, and unusual operating constraints,

(3) Identify major energy consuming systems,

(4) Review available architectural and engineering plans, 

facility operation and maintenance procedures and logs, and fuel 

usage,
44

(5) Identify a list of major energy conservation measures,

(6) Determine the energy savings potential of the energy 

conservation measures identified, and

(7) Prepare a comprehensive report detailing the ways to 

improve efficiency, the cost of specific improvements, benefits, 

and the time frame for recouping those investments.

G. What are the continuous compliance requirements?

To demonstrate continuous compliance with the emission 

limitations, we are proposing following requirements:

(1) For units combusting coal, biomass, or residual fuel 

oil (i.e., No 4, 5 or 6 fuel oil) with heat input capacities of 

less than 250 million Btu per hour that do not use a wet 

scrubber, we are proposing that opacity levels be maintained to 

less than 10 percent (daily average) for existing and new units 

with applicable emission limits. Or, if the unit is controlled 

with a fabric filter, instead of continuous monitoring opacity, 

the fabric filter must be continuously operated such that the 

bag leak detection system alarm does not sound more than 5 

percent of the operating time during any 6-month period (unless 

a PM CEMS is used).

(2) For units combusting coal, biomass, or residual oil 

with heat input capacities of 250 million Btu per hour or 

greater, we are proposing that PM CEMS be installed and operated 
45

and that PM levels (monthly average) be maintained below the 

applicable PM limit.

(3) For boilers and process heaters with wet scrubbers, we 

are proposing that you monitor pressure drop and liquid flow 

rate of the scrubber and maintain the 12-hour block averages at 

or above the operating limits established during the performance 

test. You must monitor the pH of the scrubber and maintain the 

12-hour block average at or above the operating limit 

established during the performance test to demonstrate 

continuous compliance with the HCl emission limits.

(4) For boilers and process heaters with dry scrubbers, we 

are proposing that you continuously monitor the sorbent 

injection rate and maintain it at or above the operating limits 

established during the performance tests.

(5) For boilers and process heaters having heat input 

capacities of less than 250 million Btu per hour with an ESP in 

combination with a wet scrubber, we are proposing that you 

monitor the pH, pressure drop, and liquid flow rate of the wet 

scrubber and maintain the 12-hour block averages at or above the 

operating limits established during the HCl performance test and 

that you monitor the voltage and current of the ESP collection 

plates and maintain the 12-hour block averages at or above the 
46

operating limits established during the mercury or PM 

performance test.

(6) For units that choose to comply with either the mercury 

emission limit or the HCl emission limit based on fuel analysis 

rather than on performance stack testing, we are proposing that 

you maintain daily fuel records that demonstrate that you burned 

no new fuels or fuels from a new supplier such that the mercury 

content or the chlorine content of the inlet fuel was maintained 

at or below your maximum fuel mercury content operating limit or 

your chlorine content operating limit set during the performance 

stack tests. If you plan to burn a new fuel, a fuel from a new 

mixture, or a new supplier’s fuel that differs from what was 

burned during the initial performance tests, then you must 

recalculate the maximum mercury input and/or the maximum 

chlorine input anticipated from the new fuels based on supplier 

data or own fuel analysis, using the methodology specified in 

Table 6 of this proposed rule. If the results of recalculating 

the inputs exceed the average content levels established during 

the initial test then, you must conduct a new performance 

test(s) to demonstrate continuous compliance with the applicable

emission limit.

(7) For all boilers and process heaters, we are proposing 

that you maintain daily records of fuel use that demonstrate 
47

that you have burned no materials that are considered solid 

waste. 

(8) For boilers and process heaters in any of the 

subcategories with heat input capacities greater than 100 

MMBtu/h, we are proposing that you continuously monitor CO and 

maintain the average CO emissions at or below the applicable 

limit listed in Tables 1 or 2 of this proposed rule.

If an owner or operator would like to use a control device 

other than the ones specified in this section to comply with 

this proposed rule, the owner/operator should follow the 

requirements in 40 CFR 63.8(f), which presents the procedure for 

submitting a request to the Administrator to use alternative 

monitoring.

H. What are the notification, recordkeeping and reporting 

requirements?

All new and existing sources would be required to comply 

with certain requirements of the General Provisions (40 CFR part 

63, subpart A), which are identified in Table 10 of this 

proposed rule. The General Provisions include specific 

requirements for notifications, recordkeeping, and reporting.

Each owner or operator would be required to submit a 

notification of compliance status report, as required by

§63.9(h) of the General Provisions. This proposed rule would
48

require the owner or operator to include in the notification of 

compliance status report certifications of compliance with rule

requirements.

Semiannual compliance reports, as required by §63.10(e)(3) 

of subpart A, would be required only for semiannual reporting 

periods when a deviation from any of the requirements in the 

rule occurred, or any process changes occurred and compliance 

certifications were reevaluated.

This proposed rule would require records to demonstrate 

compliance with each emission limit and work practice standard. 

These recordkeeping requirements are specified directly in the 

General Provisions to 40 CFR part 63, and are identified in 

Table 10. Owners or operators of sources with units with heat 

input capacity of less than 10 MMBtu/h or units combusting 

natural gas or refinery gas must keep records of the dates and 

the results of each required boiler tune-up.

Records of either continuously monitored parameter data for 

a control device if a device is used to control the emissions or 

CEMS data would be required.

We are proposing that you must keep the following records:

(1) All reports and notifications submitted to comply with 

this proposed rule.
49

(2) Continuous monitoring data as required in this

proposed rule.

(3) Each instance in which you did not meet each emission 

limit and each operating limit (i.e., deviations from this

proposed rule).

(4) Daily hours of operation by each source.

(5) Total fuel use by each affected source electing to 

comply with an emission limit based on fuel analysis for each 

30-day period along with a description of the fuel, the total 

fuel usage amounts and units of measure, and information on the 

supplier and original source of the fuel.

(6) Calculations and supporting information of chlorine 

fuel input, as required in this proposed rule, for each affected 

source with an applicable HCl emission limit.

(7) Calculations and supporting information of mercury 

fuel input, as required in this proposed rule, for each affected 

source with an applicable mercury emission limit.

(8) A signed statement, as required in this proposed rule, 

indicating that you burned no new fuel type and no new fuel 

mixture or that the recalculation of chlorine input demonstrated

that the new fuel or new mixture still meets chlorine fuel input 

levels, for each affected source with an applicable HCl emission 

limit.
50

(9) A signed statement, as required in this proposed rule, 

indicating that you burned no new fuels and no new fuel mixture 

or that the recalculation of mercury fuel input demonstrated

that the new fuel or new fuel mixture still meets the mercury 

fuel input levels, for each affected source with an applicable 

mercury emission limit.

(10) A copy of the results of all performance tests, fuel 

analysis, opacity observations, performance evaluations, or 

other compliance demonstrations conducted to demonstrate initial 

or continuous compliance with this proposed rule.

(11) A copy of your site-specific monitoring plan 

developed for this proposed rule as specified in 63 CFR 63.8(e), 

if applicable.

We are also proposing to require that you submit the 

following reports and notifications:

(1) Notifications required by the General Provisions.

(2) Initial Notification no later than 120 calendar days 

after you become subject to this subpart.

(3) Notification of Intent to conduct performance tests 

and/or compliance demonstration at least 60 calendar days before 

the performance test and/or compliance demonstration is 

scheduled.
51

(4) Notification of Compliance Status 60 calendar days 

following completion of the performance test and/or compliance 

demonstration.

(5) Compliance reports semi-annually.

I. Submission of Emissions Test Results to EPA

The EPA must have performance test data to conduct 

effective reviews of CAA Section 112 and 129 standards, as well 

as for many other purposes including compliance determinations, 

emissions factor development, and annual emissions rate 

determinations. In conducting these required reviews, we have 

found it ineffective and time consuming not only for us but also 

for regulatory agencies and source owners and operators to 

locate, collect, and submit emissions test data because of 

varied locations for data storage and varied data storage 

methods. One improvement that has occurred in recent years is 

the availability of stack test reports in electronic format as a 

replacement for cumbersome paper copies. 

In this action, we are taking a step to improve data 

accessibility. Owners and operators of boilers and process 

heaters will be required to submit to an EPA electronic database 

an electronic copy of reports of certain performance tests 

required under this rule. Data entry will be through an 

electronic emissions test report structure called the Electronic 
52

Reporting Tool (ERT) that will be used by the staff as part of 

the emissions testing project. The ERT was developed with input 

from stack testing companies who generally collect and compile 

performance test data electronically and offices within State 

and local agencies which perform field test assessments. The 

ERT is currently available, and access to direct data submittal 

to EPA’s electronic emissions database (WebFIRE) will become 

available by December 31, 2011.

The requirement to submit source test data electronically 

to EPA will not require any additional performance testing and 

will apply to those performance tests conducted using test 

methods that are supported by ERT. The ERT contains a specific 

electronic data entry form for most of the commonly used EPA 

reference methods. The website listed below contains a listing 

of the pollutants and test methods supported by ERT. In 

addition, when a facility submits performance test data to 

WebFIRE, there will be no additional requirements for emissions 

test data compilation. Moreover, we believe industry will 

benefit from development of improved emissions factors, fewer 

follow-up information requests, and better regulation 

development as discussed below. The information to be reported 

is already required for the existing test methods and is 

necessary to evaluate the conformance to the test method. 
53

One major advantage of submitting source test data through 

the ERT is that it provides a standardized method to compile and 

store much of the documentation required to be reported by this 

rule while clearly stating what testing information we require. 

Another important benefit of submitting these data to EPA at the 

time the source test is conducted is that it will substantially 

reduce the effort involved in data collection activities in the 

future. Specifically, because EPA would already have adequate 

source category data to conduct residual risk assessments or 

technology reviews, there would be fewer or less substantial 

data collection requests (e.g., CAA Section 114 letters). This 

results in a reduced burden on both affected facilities (in 

terms of reduced manpower to respond to data collection 

requests) and EPA (in terms of preparing and distributing data 

collection requests). 

State/local/Tribal agencies may also benefit in that their 

review may be more streamlined and accurate as the States will 

not have to re-enter the data to assess the calculations and 

verify the data entry. Finally, another benefit of submitting 

these data to WebFIRE electronically is that these data will 

improve greatly the overall quality of the existing and new 

emissions factors by supplementing the pool of emissions test 

data upon which the emissions factor is based and by ensuring 
54

that data are more representative of current industry 

operational procedures. A common complaint we hear from 

industry and regulators is that emissions factors are outdated 

or not representative of a particular source category. 

Receiving and incorporating data for most performance tests will 

ensure that emissions factors, when updated, represent 

accurately the most current operational practices. In summary, 

receiving test data already collected for other purposes and 

using them in the emissions factors development program will 

save industry, State/local/Tribal agencies, and EPA time and 

money and work to improve the quality of emissions inventories 

and related regulatory decisions.

As mentioned earlier, the electronic data base that will be 

used is EPA’s WebFIRE, which is a Web site accessible through 

EPA’s Technology Transfer Network (TTN). The WebFIRE Web site 

was constructed to store emissions test data for use in 

developing emissions factors. A description of the WebFIRE data 

base can be found at 

http://cfpub.epa.gov/oarweb/index.cfm?action=fire.main.

The ERT will be able to transmit the electronic report through 

EPA’s Central Data Exchange (CDX) network for storage in the 

WebFIRE data base. Although ERT is not the only electronic 

interface that can be used to submit source test data to the CDX 
55

for entry into WebFIRE, it makes submittal of data very 

straightforward and easy. A description of the ERT can be found 

at http://www.epa.gov/ttn/chief/ert/ert_tool.html. 

IV. Rationale for this Proposed Rule

A. How did EPA determine which sources would be regulated under 

this proposed rule?

This proposed rule regulates source categories covering 

industrial boilers, institutional and commercial boilers, and 

process heaters. These source categories potentially include 

combustion units that are already regulated by other MACT 

standards under CAA sections 112 or 129. Therefore, we are 

excluding from this proposed rule any units that are subject to 

regulation in another MACT standard established under CAA 

section 112 or a standard established under CAA section 129.

The CAA specifically requires that fossil fuel-fired steam 

generating units of more than 25 megawatts that produce 

electricity for sale (i.e., utility boilers) be reviewed 

separately by EPA. Consequently, this proposed rule would not 

regulate fossil fuel-fired utility boilers greater than 25 

megawatts, but would regulate fossil fuel-fired units less than 

25 megawatts and all utility boilers firing a non-fossil fuel 

that is not a solid waste.
56

The scope of the process heater source category is limited 

to only indirect-fired units2

The proposed rule would not regulate hot water heaters, as 

defined in this proposed rule, because such units are not part 

of the listed source categories. Many industrial facilities 

have office buildings located onsite which use hot water 

heaters. Such hot water heaters, by their design and operation, 

could be considered boilers since hot water heaters meet the 

definition of a boiler as specified in the proposed rule,

because they are enclosed devices that combust fuel for the 

purpose of recovery energy to heat water. However, hot water 

heaters are more appropriately described as residential-type 

boilers, not industrial, commercial or institutional boilers

. Direct-fired units are covered in 

other MACT standards or rulemakings pertaining to industrial 

process operations. For example, lime kilns are covered by the 

Pulp and Paper NESHAP (40 CFR part 63, subpart S). Indirectfired process heaters are similar to boilers in fuel use, 

emissions, and applicable controls, and, therefore, it is 

appropriate for EPA to combine this listed source category of

units with the listed sources categories of industrial boilers 

and commercial/institutional boilers for purposes of developing 

emission standards.

 

2 Indirect-fired process heaters are combustion devices in which the combustion gases do not directly come into 

contact with process materials.
57

because their output (i.e., hot water) is intended for personal 

use rather than for use in an industrial, commercial, or 

institutional process. Moreover, since hot water heaters 

generally are small and use natural gas as fuel, their emissions 

are negligible compared to the emissions from the industrial 

operations that make such facilities major sources, and compared 

to boilers that are used for industrial, commercial, or 

institutional purposes. However, the primary reason that we are 

excluding hot water heaters is that hot water heaters are not 

part of the listed source category. Consequently, we are 

including a definition of hot water heaters that includes fuel, 

size, pressure and temperature limitations that we believe are 

appropriate to distinguish between residential-type units and 

industrial, commercial or institutional units.

The CAA allows EPA to divide source categories into 

subcategories based on differences in class, type, or size. For 

example, differences between given types of units can lead to 

corresponding differences in the nature of emissions and the 

technical feasibility of applying emission control techniques. 

The design, operating, and emissions information that EPA has

reviewed indicates differences in unit design that distinguish 

different types of boilers. Data indicate that there are
58

significant design and operational differences between units 

that burn coal, biomass, liquid and gaseous fuels.

Boiler systems are designed for specific fuel types and 

will encounter problems if a fuel with characteristics other 

than those originally specified is fired. While many boilers in 

the population database are indicated to co-fire liquids or 

gases with solid fuels, in actuality most of these commonly use 

fuel oil or natural gas as a startup fuel only, and operate on 

solid fuel during the remainder of their operation. In 

contrast, some co-fired units are specifically designed to fire 

combinations of solids, liquids, and gases. Changes to the fuel 

type would generally require extensive changes to the fuel 

handling and feeding system (e.g., a stoker using wood as fuel 

would need to be redesigned to handle fuel oil or gaseous fuel). 

Additionally, the burners and combustion chamber would need to 

be redesigned and modified to handle different fuel types and 

account for increases or decreases in the fuel volume. In some 

cases, the changes may reduce the capacity and efficiency of the 

boiler or process heater. An additional effect of these changes 

would be extensive retrofitting needed to operate using a 

different fuel.

The design of the boiler or process heater, which is 

dependent in part on the type of fuel being burned, impacts the 
59

degree of combustion. Boilers and process heaters emit a number 

of different types of HAP emissions. Organic HAP are formed 

from incomplete combustion and are influenced by the design and 

operation of the unit. The degree of combustion may be greatly 

influenced by three general factors: time, turbulence, and 

temperature. On the other hand, the formation of fuel dependent 

HAP (metals, mercury, and acid gases) is dependent upon the 

composition of the fuel. These fuel dependent HAP emissions 

generally can be controlled by either changing the fuel property 

before combustion or by removing the HAP from the flue gas after 

combustion.

We first examined the HAP emissions results to determine if 

subcategorization by unit design type was warranted. We 

concluded that the data were sufficient for determining that a 

distinguishable difference in performance exists based on unit 

design type. Therefore, because different types of units have 

different emission characteristics which may influence the 

feasibility of effectiveness of emission control, they should be

regulated separately (i.e., subcategorized). Accordingly, we

propose to subcategorize boilers and process heaters based on 

unit design in order to account for these differences in 

emissions and applicable controls.
60

For the fuel-dependent HAP (metals, mercury, acid gases), 

we identified five basic unit types as subcategories. These are 

the following: (1) units designed to burn coal, (2) units 

designed to burn biomass, (3) units designed to burn liquid 

fuel, (4) units designed to burn natural gas/refinery gas, and

(5) units designed to burn other process gases. Within the 

basic unit types there are different designs and combustion 

systems, while having a minor effect on fuel-related HAP 

emissions, that have a much larger effect on organic HAP 

emissions. Therefore, we decided to further subcategorize based 

on these different unit designs but only in proposing standards 

for organic HAP emissions. We have identified the following 10

subcategories for organic HAP:

Pulverized coal units,

Stokers designed to burn coal,

Fluidized bed units designed to burn coal,

Stokers designed to burn biomass,

Fluidized bed units designed to burn biomass,

Suspension burners/Dutch Ovens designed to burn biomass,

Fuel Cells designed to burn biomass,

Units designed to burn liquid fuel,

Units designed to burn natural gas/refinery gas, and

Units designed to burn other gases.
61

These subcategories are based on the primary fuel that the 

boiler or process heater is designed to burn. We are aware that 

some boilers burn a combination of fuel types or burn a 

different fuel type as a backup fuel if the primary fuel supply 

is curtailed. However, boilers are designed based on the 

primary fuel type (and perhaps to burn a backup fuel) and can 

encounter operational problems if another fuel type that was not 

considered in its design is fired at more than 10 percent of the 

heat input to the boiler. Also, in some cases, a small amount 

of coal may be added to a biomass designed boiler to stabilize 

the combustion when the biomass has a higher moisture content 

than normal. In this case, it would not be appropriate to 

classify the boiler as being in one of the “coal” subcategories

because the boiler design is such that it is constructed and 

operated to combust biomass, and could not combust primarily 

coal (without significant retrofitting or design changes). 

Therefore, we are proposing to define boilers and process 

heaters that burn more than 10 percent coal (on an annual heat 

input basis) as being in one of the coal subcategories. We are 

also proposing to define boilers and process heaters that burn 

more than 10 percent biomass, and less than 10 percent coal, (on 

an annual heat input basis) as being in one of the biomass 

subcategories. We are proposing to define boilers and process 
62

heaters that burn more than 10 percent liquid fuel, and less 

than 10 percent solid fuel, (on an annual heat input basis) as 

being in the liquid subcategory. We are proposing to define 

boilers and process heaters that burn more than 90 percent 

natural gas and/or refinery gas (on an annual heat input basis) 

as being in the Gas 1 subcategory. This would ensure that each 

boiler and process heater is subject to emissions standards 

calculated on the basis of the best performing units with 

similar design and operation. The remaining boilers and process 

heaters, except for those described below would be in the Gas 2 

subcategory.

In addition, there is a certain class of natural gas-fired 

process heaters that are designed and operated in such a manner 

that are different compared to typical process heaters. A 

review of information gathered on process heaters used in the 

metal processing industries shows that these process heaters 

typically are designed with multiple burners that fired into 

individual combustion chambers. These individual burners are 

operated to cycle on and off to maintain the proper temperatures 

throughout the various zones of the process heater. Thus, due 

to their design, these process heaters rarely operate in a 

steady-state condition due to burners constantly starting up and 

shutting down resulting in emissions characteristics different 
63

from the process heaters used in other industries. The process 

heaters used in metal processing are natural gas-fired and 

include annealing furnaces, preheat furnaces, reheat furnaces, 

aging furnaces, and heat treat furnaces. Therefore, we propose 

to identify these metal processing process heaters (furnaces) as 

a separate eleventh subcategory. 

In summary, we have identified 11 subcategories of boilers 

and process heaters located at major sources.

B. How did EPA select the format for this proposed rule?

This proposed rule includes numerical emission limits for 

PM, mercury, HCl, CO, and D/F. The selection of numerical 

emission limits as the format for this proposed rule provides 

flexibility for the regulated community by allowing a regulated 

source to choose any control technology or technique to meet the 

emission limits, rather than requiring each unit to use a 

prescribed control method that may not be appropriate in each 

case.

We are proposing numerical emission rate limits as a mass 

of pollutant emitted per heat energy input to the boiler or 

process heater for the fuel-related HAP. The most typical units 

for the limits are pounds of pollutant emitted per million Btu 

of heat input. The mass per heat input units are consistent 
64

with other Federal and many State boiler regulations3

We are proposing outlet concentration as the format for the 

organic HAP. An outlet concentration limit for organic HAP 

would also be consistent with the format of other regulations.

and allows 

easy comparison between such requirements. Additionally, this

proposed rule contains an option to monitor inlet chlorine and

mercury content in the fuel to meet outlet emission rate limits. 

This option can only be done on a mass basis.

Boilers and process heaters can emit a wide variety of 

compounds, depending on the fuel burned. Because of the large 

number of HAP potentially present and the disparity in the 

quantity and quality of the emissions information available, EPA 

grouped the HAP into five categories: mercury, non-mercury 

metallic HAP, inorganic HAP, non-dioxin organic HAP, and D/F. 

The pollutants within each group have similar characteristics 

and can be controlled with the same techniques. For example, 

non-mercury metallic HAP can be controlled with PM controls. We

chose to look at mercury separately from other metallic HAP due 

to its different chemical characteristics and its different 

control technology feasibility.

Next, EPA identified compounds that could be used as 

surrogates for all the compounds in each pollutant category. 

 

3 For example, the new source performance standards for industrial, commercial, and institutional steam generating 

units (40 CFR subpart Db) have emission limits for sulfur dioxide, nitrogen oxide, and PM in terms of pounds per 

million Btu. 
65

For the non-mercury metallic HAP, we chose to use PM as a 

surrogate. Most, if not all, non-mercury metallic HAP emitted 

from combustion sources will appear on the flue gas fly-ash. 

Therefore, the same control techniques that would be used to 

control the fly-ash PM will control non-mercury metallic HAP. 

PM was also chosen instead of specific metallic HAP because all 

fuels do not emit the same type and amount of metallic HAP but 

most generally emit PM that includes some amount and combination 

of metallic HAP. The use of PM as a surrogate will also 

eliminate the cost of performance testing to comply with 

numerous standards for individual non-mercury metals. Since 

non-mercury metallic HAP tend to be on small size particles 

(i.e., fine particle enrichment), we considered using PM2.5 as 

the surrogate but we determined that PM (filterable) was the 

more appropriate surrogate for two reasons. First, the test 

method (OTM 27) for measuring PM2.5 is only applicable for use in 

exhaust stacks without entrained water droplets. Therefore, the 

test method (OTM 27) for measuring PM2.5 is not applicable for 

units equipped with wet scrubbers which will likely be necessary 

to achieve the proposed HCl emission limits. Second, based on 

the emission data obtained, during EPA’s information collection 

effort, from units not equipped with wet scrubbers, the majority 

of the filterable PM emitted from units that are well controlled
66

for PM is fine particulate (PM2.5). Thus, we are proposing to 

use PM (filterable), instead of PM2.5, as the surrogate for nonmercury metals. 

For inorganic HAP, EPA is proposing using HCl as a 

surrogate. The emissions test information available to EPA 

indicate that the primary inorganic HAP emitted from boilers and 

process heaters are acid gases, with HCl present in the largest 

amounts. Other inorganic compounds emitted are found in much 

smaller quantities. Control technologies that reduce HCl also 

control other inorganic compounds such as chlorine and other

acid gases. Thus, the best controls for HCl would also be the 

best controls for other inorganic HAP that are acid gases. 

Therefore, HCl is a good surrogate for inorganic HAP because 

controlling HCl will result in control of other inorganic HAP 

emissions.

For organic HAP, we considered both THC and CO as a 

surrogate for non-dioxin organic HAP emitted from boilers and 

process heaters. CO has generally been used as a surrogate for 

organic HAP because CO is a good indicator of incomplete 

combustion and organic HAP are products of incomplete 

combustion. However, based on concerns that CO may not be an 

appropriate surrogate for D/F because, unlike other organic HAP,

D/F can be formed outside the combustion unit, we are proposing 
67

to use CO as a surrogate for non-dioxin organic HAP. We are 

also proposing a separate emission limits for D/F. For nondioxin organic HAP, using CO as a surrogate is a reasonable 

approach because minimizing CO emissions will result in 

minimizing non-dioxin organic HAP. Methods used for the control 

of non-dioxin organic HAP emissions would be the same methods 

used to control CO emissions. These emission control methods 

include achieving good combustion or using an oxidation

catalyst. Standards limiting emissions of CO will also result 

in decreases in non-dioxin organic HAP emissions (with the

additional benefit of decreasing volatile organic compounds 

(VOC) emissions). Establishing emission limits for specific 

organic HAP (with the exception of D/F) would be impractical and 

costly. CO, which is less expensive to test for and monitor, is 

appropriate for use as a surrogate for non-dioxin organic HAP.

The Agency recognizes that the level and distribution of 

organic HAP associated with CO emissions will vary from unit to 

unit. For example, the principal organic HAP emitted from coalfired units is benzene accounting for 20 percent of the organic 

HAP while the principal organic HAP emitted from biomass-fired 

units is formaldehyde accounting for 34 percent of the organic 

HAP. Limiting CO as a surrogate for only non-dioxin organic HAP 

will eliminate costs associated with speciating numerous 
68

compounds. The proposed standards establish separate emission 

limits for D/F because of the high toxicity associated with even

low masses of these compounds.

THC could also be an appropriate surrogate for non-dioxin 

organic HAP because low THC also ensures good combustion 

efficiency and, thus, low organic HAP. However, we believe CO 

is preferable because many sources currently have CO CEMS. In 

addition, there are more CO emission data available for the 

various subcategories than THC emission data. 

C. How did EPA determine the proposed emission limitations for 

existing units?

All standards established pursuant to CAA section 112(d)(2) 

must reflect MACT, the maximum degree of reduction in emissions 

of air pollutants that the Administrator, taking into 

consideration the cost of achieving such emissions reductions, 

and any nonair quality health and environmental impacts and 

energy requirements, determined is achievable for each category. 

For existing sources, MACT cannot be less stringent than the 

average emission limitation achieved by the best performing 12 

percent of existing sources for categories and subcategories 

with 30 or more sources or the best performing 5 sources for 

subcategories with less than 30 sources. This requirement 

constitutes the MACT floor for existing boilers and process 
69

heaters. However, EPA may not consider costs or other impacts 

in determining the MACT floor. EPA must consider cost, nonair 

quality health and environmental impacts, and energy 

requirements in connection with any standards that are more 

stringent than the MACT floor (beyond-the-floor controls).

D. How did EPA determine the MACT floor for existing units?

EPA must consider available emissions information to 

determine the MACT floor. We calculated the MACT floor for a 

subcategory of sources by ranking all the available emissions 

data from units within the subcategory from lowest emissions to 

highest emissions, and then taking the numerical average of the 

test results from the best performing (lowest emitting) 12 

percent of sources.

We first considered whether fuel switching would be an 

appropriate control option for sources in each subcategory. We 

considered the feasibility of fuel switching to other fuels used 

in the subcategory and to fuels from other subcategories. This

consideration included determining whether switching fuels would 

achieve lower HAP emissions. A second consideration was whether 

fuel switching could be technically achieved by boilers and 

process heaters in the subcategory considering the existing

design of boilers and process heaters. We also considered the 

availability of various types of fuel.
70

After considering these factors, we determined that fuel 

switching was not an appropriate control technology for purposes 

of determining the MACT floor level of control for any

subcategory. This decision was based on the overall effect of 

fuel switching on HAP emissions, technical and design

considerations discussed previously in this preamble, and 

concerns about fuel availability.

Based on the data available in the emissions database, we 

determined that while fuel switching from solid fuels to gaseous 

or liquid fuels would decrease PM and some metals emissions,

emissions of some organic HAP would increase. This

determination is discussed in the memorandum “Development of 

Fuel Switching Costs and Emission Reductions for Industrial, 

Commercial, and Institutional Boilers and Process Heaters 

National Emission Standards for Hazardous Air Pollutants”

located in the docket.

A similar determination was made when considering fuel 

switching to cleaner fuels within a subcategory. For example, 

the term “clean coal” refers to coal that is lower in sulfur 

content and not necessarily lower in HAP content. Data gathered 

by EPA also indicates that within specific coal types HAP 

content can vary significantly. Switching to a low sulfur coal 

may actually increase emissions of some HAP. Therefore, it is
71

not appropriate for EPA to include fuel switching to a low 

sulfur coal as part of the MACT standards for boilers and

process heaters. Fuel switching from coal to biomass would 

result in similar impacts on HAP emissions. While this would 

reduce metallic HAP emissions, it would likely increase 

emissions of organics based on information in the emissions 

database. 

Another factor considered was the availability of 

alternative fuel types. Natural gas pipelines are not available

in all regions of the U.S., and natural gas is simply not 

available as a fuel for many industrial, commercial, and

institutional boilers and process heaters. Moreover, even where 

pipelines provide access to natural gas, supplies of natural gas 

may not be adequate. For example, it is common practice in 

cities during winter months (or periods of peak demand) to 

prioritize natural gas usage for residential areas before 

industrial usage. Requiring boilers and process heaters to 

switch to natural gas would place an even greater strain on 

natural gas resources. Consequently, even where pipelines 

exist, some units would not be able to run at normal or full 

capacity during these times if shortages were to occur. 

Therefore, under any circumstances, there would be some units 
72

that could not comply with a requirement to switch to natural

gas.

Similar problems for fuel switching to biomass could arise. 

Existing sources burning biomass generally are combusting a 

recovered material from the manufacturing or agriculture

process. Industrial, commercial, and institutional facilities 

that are not associated with the wood products industry or 

agriculture may not have access to a sufficient supply of 

biomass materials to replace their fossil fuel.

As discussed previously in this preamble, there is a 

significant concern that switching fuels would be infeasible for 

sources designed and operated to burn specific fuel types. 

Changes in the type of fuel burned by a boiler or process heater 

(solid, liquid, or gas) may require extensive changes to the 

fuel handling and feeding system (e.g., a stoker using wood as 

fuel would need to be redesigned to handle fuel oil or gaseous 

fuel). Additionally, burners and combustion chamber designs are

generally not capable of handling different fuel types, and 

generally cannot accommodate increases or decreases in the fuel 

volume. Design changes to allow different fuel use, in some 

cases, may reduce the capacity and efficiency of the boiler or

process heater. Reduced efficiency may result in less complete 

combustion and, thus, an increase in organic HAP emissions. For 
73

the reasons discussed above, we decided that fuel switching to

cleaner solid fuels or to liquid or gaseous fuels is not an 

appropriate criteria for identifying the MACT floor level of 

control for units in the boilers and process heaters category.

Therefore, the MACT floor limits for each of the HAP and 

HAP surrogates (PM, mercury, CO, HCl, and D/F) are calculated 

based on the performance of the lowest emitting (best

performing) sources in each of the subcategories. We ranked all 

of the sources for which we had data based on their emissions 

and identified the lowest emitting 12 percent of the sources for 

each HAP.

We used the emissions data for those best performing 

affected sources to determine the emission limits to be 

proposed, with an accounting for variability. EPA must exercise 

its judgment, based on an evaluation of the relevant factors and 

available data, to determine the level of emissions control that 

has been achieved by the best performing sources under variable 

conditions. The DC Circuit Court of Appeals has recognized that 

EPA may consider variability in estimating the degree of 

emission reduction achieved by best-performing sources and in 

setting MACT floors. See Mossville Envt’l Action Now v. EPA, 

370 F.3d 1232, 1241–42 (D.C. Cir 2004) (holding EPA may consider 

emission variability in estimating performance achieved by best-
74

performing sources and may set the floor at level that bestperforming source can expect to meet “every day and under all 

operating conditions”). 

In determining the MACT floor limits, we first determine 

the floor, which is the level achieved in practice by the 

average of the top 12 percent. We then assess variability of 

the best performers by using a statistical formula designed to 

estimate a MACT floor level that is achievable by the average of 

the best performing sources if the best performing sources were 

able to replicate the compliance tests in our data base. 

Specifically, the MACT floor limit is an upper prediction limit 

(UPL) calculated with the Student’s t-test using the TINV 

function in Microsoft Excel. The Student’s t-test has also been 

used in other EPA rulemakings (e.g., NSPS for 

Hospital/Medical/Infectious Waste Incinerators) in accounting 

for variability. A prediction interval for a future observation 

is an interval that will, with a specified degree of confidence, 

contain the next (or some other pre-specified) randomly selected 

observation from a population. In other words, the prediction 

interval estimates what future values will be, based upon 

present or past background samples taken. Given this 

definition, the UPL represents the value which we can expect the 

mean of 3 future observations (3-run average) to fall below, 
75

based upon the results of a independent sample from the same 

population. In other words, if we were to randomly select a 

future test condition from any of these sources (i.e., average 

of 3 runs), we can be 99% confident that the reported level will 

fall at or below the UPL value. To calculate the UPL, we used 

the average (or sample mean) and sample standard deviation, 

which are two statistical measures calculated from the sample 

data. The average is the central value of a data set, and the 

standard deviation is the common measure of the dispersion of 

the data set around the average.

We first determined the distribution of the emissions data 

for the best-performing 12 percent of units within each 

subcategory prior to calculating UPL values. To evaluate the 

distribution of the best performing dataset, we first computed 

the skewness and kurtosis statistics and then conducted the 

appropriate small-sample hypothesis tests.

The skewness statistic (S) characterizes the degree of 

asymmetry of a given data distribution. Normally distributed 

data have a skewness of 0. A skewness statistic that is greater 

(less) than 0 indicates that the data are asymmetrically 

distributed with a right (left) tail extending towards positive 

(negative) values. Further, the standard error of the skewness 

statistic (SES) is given by SES = SQRT(6/N) where N is the 
76

sample size. According to the small sample skewness hypothesis 

test, if the skewness statistic (S) is greater than two times 

the SES, the data distribution can be considered non-normal. 

The kurtosis statistic (K) characterizes the degree of 

peakedness or flatness of a given data distribution in 

comparison to a normal distribution. Normally distributed data 

have a kurtosis of 0. A kurtosis statistic that is greater 

(less) than 0 indicates a relatively peaked (flat) distribution. 

Further, the standard error of the kurtosis statistic (SEK) is 

given by SEK = SQRT(24/N) where N is the sample size. According 

to the small sample kurtosis hypothesis test, if the kurtosis

statistic (K) is greater than two times the SEK, the data 

distribution is typically considered to be non-normal.

We applied the skewness and kurtosis hypothesis tests to 

both the reported test values and the lognormal values of the 

reported test values. If the skewness (S) and kurtosis (K) 

statistics of the reported data set were both less than twice 

the SES and SEK, respectively, the dataset was classified as 

normally distributed. If neither of the skewness (S) and 

kurtosis (K) statistics, or only one of these statistics were 

less than twice the SES or SEK, respectively, then the skewness 

and kurtosis hypothesis tests were conducted for the natural 

log-transformed data. Then the distribution most similar to a 
77

normal distribution was selected as the basis for calculating 

the UPL. If both the reported values and the natural-log 

transformed reported values had skewness (S) and kurtosis (K) 

statistics that were greater than twice the SES or SEK, 

respectively, the normally distributed dataset was selected as

the basis of the floor to be conservative. If the results of 

the skewness and kurtosis hypothesis tests were mixed for the 

reported values and the natural log-transformed reported values, 

we also chose the normal distribution to be conservative. We 

believe this approach is more accurate and obtained more 

representative results than a more simplistic normal 

distribution assumption.

Since the compliance with the MACT floor emission limit is 

based on the average of a three run test, the UPL is calculated 

by:

Where:

n = the number of test runs

m = the number of test runs in the compliance average

This calculation was performed using the following two Excel 

functions:

Normal distribution: 99% UPL = AVERAGE(Test Runs in Top 12%) + 

[STDEV(Test Runs in Top 12%) x TINV(2 x probability, n-1 degrees 

of freedom)*SQRT((1/n)+(1/3))], for a one-tailed t-value (with 2 

x probability), probability of 0.01, and sample size of n 
78

Lognormal distribution: 99% UPL = EXP{AVERAGE(Natural Log 

Values of Test Runs in Top 12%) + [STDEV(Natural Log Values of 

Test Runs in Top 12%) x TINV(2 x probability, n-1 degrees of 

freedom)* SQRT((1/n)+(1/3))]}, for a one-tailed t-value (with 2 

x probability), probability of 0.01, and sample size of n

We are requesting comment on whether there is a more appropriate 

statistical approach to account for variability in the MACT 

floor analyses when there are emission data from a limited 

number of units in the subcategory.

However, after review of the available HAP data, including 

both emission test data and fuel analyses, we determined that it 

was inappropriate to use only this MACT floor approach to 

determine variability and to establish emission limits for 

boilers and process heaters, because this approach considers 

only the emissions test data. The main problem with using only 

the HAP emissions test data is that the data, which may reflect 

the variability of fuel-related HAP of the best performing 

units, may not reflect the variability of fuel-related HAP from 

the best performing units over the long term. Based on fuelrelated HAP concentrations (nine individual samples collected 

over a 30-day period) obtained, pursuant to letters mandating

data gathering issued under the authority of CAA section 114, 

fuel-related HAP levels in the various fuels can vary

significantly over time. 
79

The first step in establishing a MACT standard is to 

determine the MACT floor. A necessary step in doing so is

determining the amount of HAP emitted. In the case of fuelrelated HAP emitted, this is not necessarily a straightforward 

undertaking. Single stack measurements represent a snapshot in 

time of a source’s emissions, always raising questions of how 

representative such emissions are of the source’s emissions over 

time. The variations in fuel-related HAP inputs directly

translate to a variability of fuel-related HAP stack emissions.

We believe that single short term stack test data 

(typically a few hours) are probably not indicative of long term 

emissions performance, and so are not the best indicators of

performance over time. With these facts in mind, we carefully 

considered alternatives other than use of only single short-term 

stack test results to quantify performance for fuel-related HAP. 

We decided that the most accurate method available to us to 

determine long term fuel-related HAP emissions performance was 

to use data on the fuel-related HAP inputs in the fuels used by 

the best performing units, obtained as part of our information 

collection effort under the authority of CAA section 114, on 

long-term fuel-related HAP concentrations (nine individual 

samples collected over a 30-day period) in each fuel, along with 

the fuel-related HAP concentrations during the stack tests.
80

As previously discussed above, we account for variability 

in setting floors, not only because variability is an element of 

performance, but because it is reasonable to assess best 

performance over time. Here, for example, we know that the HAP 

emission data from the best performing units are short-term 

averages, and that the actual HAP emissions from those sources 

will vary over time. If we do not account for this variability, 

we would expect that even the units that perform better than the

floor on average would potentially exceed the floor emission 

levels a significant part of the time which would mean that 

variability was not properly taken into account. This 

variability includes the day-to-day variability in the total

fuel-related HAP input to each unit and variability of the 

sampling and analysis methods, and it includes the variability 

resulting from site-to-site differences for the best performing 

units. We calculated the MACT floor based on the UPL (upper 

99th percentile) as described earlier from the average 

performance of the best performing units, Students t-factor, and 

the variability of the best performing units.

This approach reasonably ensures that the emission limit 

selected as the MACT floor adequately represents the level of 

emissions actually achieved by the average of the units in the 

top 12 percent, considering ordinary operational variability of 
81

those units. Both the analysis of the measured emissions from 

units representative of the top 12 percent, and the variability 

analysis, are reasonably designed to provide a meaningful 

estimate of the average performance, or central tendency, of the 

best controlled 12 percent of units in a given subcategory. 

A detailed discussion of the MACT floor methodology is 

presented in the memorandum “MACT Floor Analysis for the 

Industrial, Commercial, and Institutional Boilers and Process 

Heaters National Emission Standards for Hazardous Air 

Pollutants” in the docket.

1. Determination of MACT for the Fuel-related HAP

In developing the proposed MACT floor for the fuel-related 

HAP (PM, HCl, and mercury), as described earlier, we are using

PM as a surrogate for non-mercury metallic HAP and HCl as a 

surrogate for the acid gases. Table 2 of this preamble presents

the number of units in each of the five subcategories, along 

with the number of units from which we have collected emission 

data. Table 2 also presents for each subcategory and fuelrelated HAP the number of units comprising the best performing 

units (top 12 percent), the average emission level of the top 12 

percent, and the MACT floor (99 percent UPL of top 12 percent) 

which includes the variability across the best performing units 

and the long term variability across those units.
82

Table 2. Summary of MACT Floor Results for the Fuel-Related HAP 

for Existing Subcategories. 

Subcategory Parameter PM

Lb/MMBtu

Mercury

Lb/MMBtu

HCl

LB/MMBtu

Units 

designed 

for Coal 

firing

No. of 

sources in 

subcategory 

=

578 578 578

No. of 

sources with 

data =

366 285 318

No. in MACT 

floor =

44 35 39

Avg of top 

12%

7.24E-03 5.95E-07 4.23E-03

99% UPL of 

top% (test 

runs) =

0.0179 1.64E-06 7.38E-03

99% UPL with 

fuel 

variability 

of top%

2.88E-06

Units 

designed 

for Biomass 

firing 

No. of 

sources in 

subcategory 

=

420 420 420

No. of 

sources with 

data =

192 91 92

No. in MACT 

floor =

24 11 12

Avg of top 

12%

6.06E-03 3.46E-07 4.34E-03

99% UPL of 

top% (test 

runs) =

0.0162 7.52E-07 6.00E-03

99% UPL with 

fuel 

variability 

of top%

8.88E-07

Units 

designed 

for Liquid 

Fuel firing

No. of 

sources in 

subcategory 

=

826 826 826
83

No. of 

sources with 

data =

91 177 190

No. in MACT 

floor =

11 22 23

Avg of top 

12%

1.40E-03 1.91E-06 2.59E-04

99% UPL of 

top% (test 

runs) =

0.00323 2.78E-06 3.26E-04

99% UPL with 

fuel 

variability 

of top%

3.97E-06

Units 

designed 

for other 

gas firing

No. of 

sources in 

subcategory 

=

199 199 199

No. of 

sources with 

data =

13 8 8

No. in MACT 

floor =

2 1 1

Avg of top 

12%

0.011 8.25E-08 1.70E-06

99% UPL of 

top% (test 

runs) =

0.045 1.86E-07 2.50E-06

 For three cases, the proposed new and existing source MACT 

floors are almost identical because the best performing 12 

percent of existing units (for which we have emissions 

information) is only one or two sources. The reason we look to 

the best performing 12 percent of sources, even though we have 

data on fewer than 5 sources, is that these subcategories

consist of 30 or more units. CAA section 112(d)(3)(A) provides 

that standards for existing sources shall not be less stringent 
84

than “the average emission limitation achieved by the best 

performing 12 percent of the existing sources (for which the 

Administrator has emissions information), * * * in the category 

or subcategory for categories and subcategories with 30 or more 

sources.” A plain reading of the above statutory provisions is 

to apply the 12 percent rule in deriving the MACT floor for 

those categories or subcategories with 30 or more sources. The 

parenthetical “(for which the Administrator has emissions 

information)” in CAA section 112(d)(3)(A) modifies the best 

performing 12 percent of existing sources, which is the clause 

it immediately follows.

 However, in cases where there are 30 or more sources but 

little emission data, this results in only a few units setting 

the existing source floor with the result that the new and 

existing source MACT floors are almost identical. In contrast, 

if these subcategories had less than 30 sources, we would be 

required to use the top five best performing sources, rather 

than the one or two that comprise the top 12 percent. Section 

112 (d)(3)(B).

 We are seeking comment on whether, with the facts of this 

rulemaking, we should consider reading the intent of Congress to 

allow us to consider five sources rather than just one or two. 

First, it seems evident that Congress was concerned that floor 
85

determinations should reflect a minimum quantum of data: At 

least data from 5 sources for source categories of less than 30 

sources (assuming that data from 5 sources exist). Second, it 

does not appear that this concern would be any less for

subcategories with 30 or more sources. We are specifically 

requesting comment on this interpretation relating to the 

proposed MACT floors.

2. Determination of MACT for Organic HAP

In developing the MACT floor for organic HAP, as described 

earlier, we are using CO as a surrogate for non-dioxin organic 

HAP. Table 3 of this preamble presents the number of units in 

each of the 11 subcategories, along with the number of units 

from which we have collected emission data. Table 3 also 

presented for each subcategory and CO and D/F the number of 

units comprising the best performing units (top 12 percent), the 

average emission level of the top 12 percent, and the MACT floor 

(99 percent UPL of top 12 percent) which includes the 

variability across the best performing units and the long term 

variability.

We calculated the MACT floors based on the upper 99th

percentile UPL from the average performance of the best 

performing units and their variances as described earlier for 

the fuel-related HAP. 
86

Table 3. Summary of MACT Floor Results for the Organic HAP 

Subcategories. 

Subcategory Parameter CO

(ppm @ 3 

percent 

oxygen)

Dioxin/Furan

(Total TEQ)

(ng/dscm @ 7 

percent 

oxygen)

Stoker –

Coal

No. of sources in 

subcategory =

361 361

No. of sources with 

data =

61 14

No. in MACT floor = 8 2

Avg of top 12% 21.4 0.00182

99% UPL of top% 

(test runs) =

48.8 0.00274

Fluidized 

Bed - Coal

No. of sources in 

subcategory =

31 31

No. of sources with 

data =

17 12

No. in MACT floor = 3 2

Avg of top 12% 12.5 0.000471

99% UPL of top% 

(test runs) =

21.4 0.00168

PC – Coal No. of sources in 

subcategory =

186 186

No. of sources with 

data =

41 10

No. in MACT floor = 5 2

Avg of top 12% 19.2 0.00158

99% UPL of top% 

(test runs) =

82.8 0.00307

Stoker –

Biomass

No. of sources in 

subcategory =

320 320

No. of sources with 

data =

119 16

No. in MACT floor = 15 2

Avg of top 12% 203 0.000819

99% UPL of top% 

(test runs) =

551 0.00339

Fluidized 

Bed –

Biomass

No. of sources in 

subcategory =

12 12

No. of sources with 7 6
87

data =

No. in MACT floor = 5 5

Avg of top 12% 97.1 0.00507

99% UPL of top 12% 

(test runs) =

245 0.0127

Suspension 

Burner/

Dutch Oven

No. of sources in 

subcategory =

62 62

No. of sources with 

data =

17 3

No. in MACT floor = 3 1

Avg of top 12% 362 0.00952

99% UPL of top 12% 

(test runs) =

1010 0.0279

Fuel Cell –

Biomass

No. of sources in 

subcategory =

26 26

No. of sources with 

data =

16 7

No. in MACT floor = 5 5

Avg of top 12% 130 0.00552

99% UPL of top 12% 

(test runs) =

262 0.0148

Units 

designed 

for Liquid 

fuel firing

No. of sources in 

subcategory =

826 826

No. of sources with 

data =

116 17

No. in MACT floor = 14 3

Avg of top 12% 0.443 0.000733

99% UPL of top 12% 

(test runs) =

0.911 0.00182

Units 

designed 

for other 

gases 

firing

No. of sources in 

subcategory =

199 199

No. of sources with 

data =

75 5

No. in MACT floor = 9 1

Avg of top 12% 0.0737 0.00267

99% UPL of top 12% 

(test runs) =

0.134 0.00828
88

For organic HAP, as previously discussed above for the 

fuel-related, we account for variability in setting floors, not 

only because variability is an element of performance, but 

because it is reasonable to assess best performance over time. 

Here, however, we know that the organic HAP emissions will also 

vary over the operating range of the unit, unlike fuel-related 

HAP emissions. Organic HAP are combustion-related pollutants. 

That is, their levels of emissions are a function of the 

combustion process. Combustion units operate most efficiently

when operated at or near their design capacity. The combustion 

efficiency tends to decrease as the unit’s load (steam 

production) decreases. Most industrial or 

commercial/institutional units do not continuously operate at or 

near their design capacity but operate according to the 

facility’s demand for steam. Thus, operation at lower capacity 

rates must be accounted for in determining operational 

variability. 

As part of EPA’s information collection effort, we obtained 

data on organic HAP (THC and CO) from six units (two coal-fired, 

two biomass-fired, and two gas-fired) that were collected by 

using CEM over a 30-day period. All of these units were 

selected to test using CEM to provide variability information
89

because their stack test results indicated that they were among 

the best performing units.

 The CEMS data shows that CO (as a surrogate for non-dioxin 

organic HAP) from best performing units did not vary much when 

such unit is operated at below design capacity. Therefore, even 

though ICI units, due to steam demand, may operate at these low 

load conditions, no additional variability due to operating load 

needs to be accounted for since the average CO emission levels 

that include these low load conditions are within the 

variability range determined by the statistical analyses of CO 

emissions from the best performing units. Thus, to the MACT 

floor 99 percent UPL values determined from the stack test data 

for CO emissions, we are proposing to add no additional

variability factor to account for load variability. 

This approach reasonably ensures that the emission limit 

selected as the MACT floor adequately represents the average 

level of control actually achieved by units in the top 12 

percent, considering ordinary operational variability of those 

units. Both the analysis of the measured emissions from units 

representative of the top 12 percent, and the variability 

analysis of those units, are reasonably designed to provide a 

meaningful estimate of the average performance, or central 
90

tendency, of the best controlled 12 percent of units in a given 

subcategory. 

As was the case for the three fuel-dependent MACT floors, 

the proposed new and existing source MACT floors for eight

combustion-dependent subcategories are almost identical because 

the best performing 12 percent of units (for which we have 

emissions information) is only one or two sources. Again, the 

reason we look to the best performing 12 percent of sources is

that these subcategories consist of 30 or more units. In

contrast, if these subcategories had less than 30 sources, we 

would be required to use the top five best performing sources, 

rather than the one or two that comprise the top 12 percent. As 

stated previously, we are seeking comment on whether, with the 

facts of this rulemaking, we should consider reading the intent 

of Congress to allow us to consider five sources rather than 

just one, two, or three. We are specifically requesting comment 

on this interpretation relating to the proposed MACT floors.

3. Determination of the Work Practice Standard

CAA section 112(h)(1) states that the Administrator may 

prescribe a work practice standard or other requirements, 

consistent with the provisions of CAA sections 112(d) or (f), in 

those cases where, in the judgment of the Administrator, it is

not feasible to enforce an emission standard. CAA section 
91

112(h)(2)(B) further defines the term “not feasible” in this 

context to apply when “the application of measurement technology 

to a particular class of sources is not practicable due to 

technological and economic limitations.” 

The standard reference methods for measuring emissions of 

mercury, CO (as a surrogate for organic HAP), D/F, HCl (as a 

surrogate for acid gases) and PM (as a surrogate for non-mercury 

metals) are EPA Methods 29, 10, 23, 26A and 5. These methods 

are reliable but relatively expensive as a group. However, the 

methods are generally not able to accurately sample small 

diameter (less than 12 inches) stacks. For example, in these 

small diameter stacks, the conventional EPA Method 5 stack 

assembly blocks a significant portion of the cross-section of 

the duct and, if unaccounted for, could cause inaccurate 

measurements. Many existing small boilers and process heaters 

have stacks with diameters less than 12 inches. The stack 

diameter is generally related to the size of the unit. Units 

that have capacity below 10 million Btu per hour generally have 

stacks with diameters less than 12 inches. Also, many existing 

small units do not currently have sampling ports or a platform 

for accessing the exhaust stack which would require an expensive 

modification to install sampling ports and a platform.
92

We conducted a cost analysis4

The results of the analysis indicate that the annual costs 

for testing and monitoring costs alone would have a significant 

to evaluate the economic 

impact of the testing and monitoring costs that facilities with 

small units would incur to demonstrate compliance with the 

proposed emission limits. The compliance costs imposed on each 

facility would not only include the costs of the stack tests and 

monitoring equipment but would also include the capital costs of 

any installed control equipment. We estimate that the total 

capital costs of installing control equipment on the over 7,400 

small boilers and process heaters to achieve the proposed 

emission limits would be $6.3 billion. In addition to these 

costs, since many of these small units do not have test ports or 

testing platforms installed in order to conduct performance 

testing. Prior to conducting a stack test each unit would need 

to construct or rent scaffolding and install test ports. EPA 

estimates that these small sources would incur an additional 

$185 million to install test ports and rent temporary 

scaffolding. Many establishments in each industry, commercial, 

or institutional sector are associated with multiple (as many as 

a 700) small units.

 

4

Memorandum: Methodology for Estimating Impacts from Industrial, Commercial, 

and Institutional Boilers and Process Heaters at Major Sources of Hazardous 

Air Pollutant Emissions, March 23, 2010. 
93

adverse economic impact on these facilities. The severity of 

the economic impact would depend on the size of the facility. 

Based on this analysis, the Administrator has determined 

under CAA section 112(h) that it is not feasible to enforce 

emission standards for a particular class of existing boilers 

and process heaters because of the technological and economic 

limitations described above. Thus, a work practice, as 

discussed below, is being proposed to limit the emission of HAP

for existing boilers and process heaters having a heat input 

capacity of less than 10 million Btu per hour. We are 

specifically requesting comment on whether a threshold higher 

than 10 million Btu per hour meets the technical and economic 

limitations as specified in CAA section 112(h). 

For existing units, the only work practice being used that 

potentially controls HAP emissions is a tune-up. Fuel dependent 

HAP are typically controlled by removing them from the flue gas 

after combustion. The only work practices expected to minimize 

fuel dependent HAP emissions are reducing the fuel usage or fuel 

switching to a fuel type with a lower HAP content. Fuel usage 

can be reduced by improving the combustion efficiency of the 

unit, such as, by a tune-up. As combustion efficiency 

decreases, fuel usage increases to maintain energy output 

resulting in increased emissions. 
94

On the other hand, organic HAP are formed from incomplete 

combustion of the fuel. The objective of good combustion is to 

release all the energy in the fuel while minimizing losses from 

combustion imperfections and excess air. The combination of the 

fuel with the oxygen requires temperature (high enough to ignite 

the fuel constituents), mixing or turbulence (to provide 

intimate oxygen-fuel contact), and sufficient time (to complete 

the process), sometimes referred to the three Ts of combustion. 

Good combustion practice (GCP), in terms of combustion units, 

could be defined as the system design and work practices 

expected to minimize organic HAP emissions.

We have obtained information on units reported using GCP, 

as part of the information collection effort for the NESHAP. 

The data that we have suggests that units typically conduct 

tune-ups. We also reviewed state regulations and permits. The 

work practices listed in state regulations includes tune-ups (10 

states), operator training (1 state), periodic inspections (2 

States), and operation in accordance with manufacturer 

specifications (1 State). Of the units with a capacity of less 

than 10 MMBtu/h that responded to EPA’s information collection 

effort for the NESHAP, 80 percent reported conducting a tune-up 

program. Ultimately, we determine that at least 6 percent of 

the units in each of the subcategory are subject to a tune-up 
95

requirement under other applicable requirements. Therefore, the 

proposed work practice of a tune-up5

We are also proposing a work practice standard under 

section 112(h) that would require an annual tune-up for existing 

boilers and process heaters combusting natural gas or refinery 

gas. These boilers and process heaters are units included in 

the Gas 1 and metal processing furnace subcategories. We are 

specifically seeking comment on whether the application of 

measurement methodology to sources in this subcategory is 

impracticable due to technological or economic limitations, as 

specified in section 112(h)(2)(B).

program does establish the 

MACT floor for HAP emissions from existing units with a heat 

input capacity of less than 10 MMBtu/h.

This proposal is based on several reasons. First, the 

capital costs estimated for installing controls on these boilers 

and process heaters to comply with MACT limits for the five HAP 

groups is over $14 billion to install a combination system of a 

fabric filter (for PM, mercury, and D/F control) and a wet 

scrubber (for HCl control). This is higher than the estimated

combined capital cost for boilers and process heaters in the 

other subcategories to comply with the proposed emission limits. 

The projected control system needed for boilers and process 

 

5 Tune-up procedure is specified in section 63.7540 of this proposed rule and includes making adjustments to the 

burner to optimize the flame to minimize CO emissions consistent with the manufacturer’s specifications. 
96

heaters in the other subcategories is also a combined fabric 

filter/wet scrubber system.

Second, we believe that proposing emission standards for 

gas-fired boilers and process heaters that result in the need to 

employ the same emission control system as needed for the other 

fuel types would have the negative benefit of providing a 

disincentive for switching to gas as a control technique (and a 

pollution prevention technique) for boilers and process heaters 

in the other fuel subcategories. In addition, emission limits 

on gas-fired boilers and process heaters may have the negative 

benefit of providing an incentive for a facility to switch from 

gas (considered a “clean” fuel) to a “dirtier” but cheaper fuel 

(i.e., coal). It would be inconsistent with the emissions 

reductions goals of the CAA, and of section 112 in particular, 

to adopt requirements that would result in an overall increase 

in HAP emissions. We are soliciting comment on the extent to 

which natural gas facilities would be expected to switch to a 

“dirtier” fuel if emissions limits for such facilities are 

adopted.

Thus, a work practice, as discussed above for small boilers 

and process heaters, is being proposed to limit the emission of 

HAP for existing natural gas-fired and refinery gas-fired 

boilers and process heaters.
97

We request comments on whether the emission limits listed 

in Table 4 of this preamble for the Gas 1 and Metal Process 

Furnace subcategories should be promulgated. Comments should 

include detailed information regarding why emission limits for 

these gas-fired boilers and process heaters are appropriate.

Table 4. Summary of MACT Floor Results for the Gas 1 and Metal 

Process Furnace Subcategories.

Subcate

gory

Parame

ter

PM

Lb/MMB

tu

Mercury

Lb/MMBt

u

HCl

LB/MMB

tu

CO

(ppm @ 

3 

percent 

oxygen)

Dioxin/Furan

(Total TEQ)

(ng/dscm @ 

7 percent 

oxygen)

Units 

designe

d for 

NG/RG 

firing

No. of 

source

s in 

subcat

egory 

=

10,783 10,783 10,783 10,783 10,783

No. of 

source

s with 

data =

144 14 11 754 8

No. in 

MACT 

floor 

=

18 2 2 91 1

Avg of 

top 

12%

0.0038

8

1.1E-07 1.01E041.45 0.0026

99% 

UPL of 

top% 

(test 

runs) 

=

0.03 2.0E-07 0.0002 20 0.01

Metal No. of 749 749 749 749 749
98

E. How did EPA consider beyond-the-floor options for existing 

units?

Once the MACT floor determinations were done for each 

subcategory, we considered various regulatory options more 

stringent than the MACT floor level of control (i.e., 

technologies or other work practices that could result in lower 

emissions) for the different subcategories. A detailed 

description of the beyond-the-floor consideration is in the 

memorandum “Methodology for Estimating Cost and Emissions 

Impacts for Industrial, Commercial, Institutional Boilers and 

Process

ing 

Furnace

s

source

s in 

subcat

egory 

=

No. of 

source

s with 

data =

9 7 9 15 7

No. in 

MACT 

floor 

=

2 1 2 2 1

Avg of 

top 

12%

0.0047 3.3E-08 0.0001

92

0.38 0.0026

99% 

UPL of 

top% 

(test 

runs) 

=

0.02 2.0E-07 0.0004 2 0.004
99

Process Heaters National Emission Standards for Hazardous Air 

Pollutants” in the docket.

We could not identify better HAP emissions reduction 

approaches that could achieve greater emissions reductions of 

HAP than the control technology combination (fabric filter,

carbon injection, scrubber, and GCP) that we expect will be used 

to meet the MACT floor level of control. 

For each subcategory, fuel switching to natural gas is an 

option that would reduce HAP emissions. We determined that fuel 

switching was not an appropriate beyond-the-floor option. 

First, natural gas supplies are not available in some areas, and 

supplies to industrial customers can be limited during periods 

when natural gas demand exceeds supply. Additionally, the 

estimated emissions reductions that would be achieved if solid 

and liquid fuel units switched to natural gas were compared with 

the estimated cost of converting existing solid fuel and liquid 

fuel units to fire natural gas. The annualized cost of fuel 

switching was estimated to be $13.5 billion compared with $3.5 

billion under the floor approach. The emission reduction 

associated with fuel switching was estimated to be 4,303 tons 

per year for metallic HAP, 8 tons per year for mercury, and 

34783 tons per year for inorganic HAP (HCl and HF). The cost 

for fuel switching is over double the cost of the floor approach 
100

while the emission reductions associated with fuel switching are 

approximately the same. Additional detail on the calculation 

procedures is provided in the memorandum “Development (2010) of 

Fuel Switching Costs and Emissions Reductions for Industrial, 

Commercial, and Institutional Boilers and Process Heaters 

National Emission Standards for Hazardous Air Pollutants” in the 

docket.

We also considered the pollution prevention and energy 

conservation measure of an energy assessment/audit as a beyondthe-floor option for HAP emissions. An energy assessment

provides valuable information on improving energy efficiency. 

An energy assessment, or audit, is an in-depth energy study 

identifying all energy conservation measures appropriate for a 

facility given its operating parameters. An energy assessment

refers to a process which involves a thorough examination of 

potential savings from energy efficiency improvements, pollution 

prevention, and productivity improvement. Besides reducing 

operating and maintenance costs, improving energy efficiency 

reduces negative impacts on the environment and results in 

reduced emissions and improved public health. Improvement in 

energy efficiency results in decreased fuel use which results in 

a corresponding decrease in emissions (both HAP and non-HAP) 

from the combustion unit, but not necessarily a decrease in 
101

emissions of all HAP emitted. The Department of Energy has 

conducted energy assessments at selected manufacturing 

facilities and reports that facilities can reduce fuel/energy 

use by 10 to 15 percent by using best practices to increase 

their energy efficiency. Many best practices are considered 

pollution prevention because they reduce the amount of fuel 

combusted which results in a corresponding reduction in 

emissions from the fuel combustion. The most common best 

practice is simply tuning the boiler to the manufacturer’s 

specification.

The one-time cost of an energy assessment ranges from $2500 

to $55,000 depending on the size of the facility. The total 

annualized cost if each major source facility conducted an 

energy assessment is estimated at $26 million. If a facility 

implemented the cost-effective energy conservation measures 

identified in the energy assessment, it would potentially result 

in greater HAP reduction than achieved by a boiler tune-up alone

and potentially reducing HAP emissions (HCl, HF, Hg, VOC, and 

dioxin/furan) by an additional 2,300 to 4,500 tons per year. In 

addition, the costs of any energy conservation improvement will 

be offset by the cost savings in lower fuel costs. Therefore, 

we decided to go beyond the MACT floor for this proposed rule 

for the existing units. These proposed standards for existing 
102

units include the requirement of a performance of an energy 

assessment to identify cost-effective energy conservation 

measures. Since there was insufficient information to determine 

if requiring implementation of cost-effective measures were 

economically feasible, we are seeking comment on this point. 

In this proposed rule, we are defining a cost-effective 

energy conservation measure to be any measure that has a payback 

(return of investment) period of 3 years or less. This payback 

period was selected based on section 325(o)(2)(B)(iii) of the 

Energy Policy and Conservation Act which states that there is a 

presumption that an energy conservation standard is economically 

justified if the increased installed cost for a measure is less 

than three times the value of the first-year energy savings 

resulting from the measure.

We believe that an energy assessment is an appropriate 

beyond-the-floor control technology because it is one of the 

measures identified in CAA section 112(d)(2). CAA section 

112(d)(2) states that “Emission standards promulgated ... and 

applicable to new or existing sources ... is achievable ... 

through application of measures, processes, methods, systems or 

techniques including, but not limited to measures which –
103

(A) reduce the volume of, or eliminate emissions of, such 

pollutants through process changes, substitution of 

materials or other modifications,

The purpose of an energy assessment is to identify energy 

conservation measures (such as, process changes or other 

modifications to the facility) that can be implemented to reduce 

the facility energy demand which would result in reduced fuel 

use. Reduced fuel use will result in a corresponding reduction 

in HAP, and non-HAP, emissions. Thus, an energy assessment, in 

combination with the MACT emission limits will result in the 

maximum degree of reduction in emissions as required by 

112(d)(2). Therefore, we are proposing to require all existing 

sources to conduct a one-time energy assessment to identify 

cost-effective energy conservation measures. 

We are specifically requesting comment on: (1) whether our 

estimates of the assessment costs are correct; (2) is there 

adequate access to certified third party assessors; (3) are 

online tools adequate to inform the facility’s decision to make 

efficiency upgrades; (4) is the definition of “cost-effective” 

appropriate in this context since it refers to payback of energy 

saving investments without regard to the impact on HAP 

reduction; and (5) what rate of return should be used.
104

We considered proposing a beyond-the-floor requirement for 

certain sources in the natural gas and refinery gas subcategory 

(i.e., the Gas 1 subcategory). Specifically, we considered

proposing that facilities with boilers or process heaters 

combusting refinery gas install and maintain a carbon adsorber 

bed system6

 

6 Carbon adsorption of mercury can be accomplished by (a) injecting dry carbon with or without other 

dry sorbents into the offgas upstream of a PM control device (typically a baghouse), or (b ) using a fixed 

or moving bed of granular carbon through which the offgas flows. In a typical fixed bed carbon 

adsorption system, the flue gas flows through a vessel packed with a specified depth of the carbon 

granules. The bed and packing are designed to limit the linear velocity of the offgas in the bed to 

increase the contact time with the carbon. Due to the increased contact times and typically lower 

operating temperatures, better removal efficiencies can be achieved than for carbon injection. At a

to remove mercury from the refinery gas before 

combustion in a boiler or process heater. Based on data from 

the information collection effort, refinery gas contains mercury 

and additional mercury reductions can be achieved from units

combusting refinery gas. Consequently, we analyzed the mercury 

emissions reductions and additional cost of adopting this work 

practice. The annualized cost of the carbon adsorber bed system 

to treat the refinery gas prior to combustion is estimated to be 

about 1.6 billion dollars with a mercury emission reduction of 

0.8 tons. The results indicated that while additional mercury 

emissions reductions would be realized, the costs would be too 

high to consider it a feasible beyond-the-floor option. Nonair 

quality health, environmental impacts, and energy effects were 

residence time of 10 seconds in the carbon bed, virtually all of the mercury can be removed. (Ref. 

NUCON INTERNATIONAL, Inc., “ Design & Performance Characteristics of MERSORBB Mercury

Adsorbents in Liquids and Gases,” NUCON 11B28, August 1995.)
105

not significant factors, because there would be little 

difference in the nonair quality health and environmental 

impacts of requiring the installation of carbon bed adsorbers. 

Therefore, we are not proposing installation of a carbon 

adsorber bed system as a beyond-the-floor requirement. 

F. Should EPA consider different subcategories for solid fuel 

boilers and process heaters?

The boilers and process heaters source category is 

tremendously heterogeneous. EPA has attempted to identify 

subcategories that provide the most reasonable basis for 

grouping and estimating the performance of generally similar 

units using the available data. We believe that the 

subcategories we selected are appropriate.

EPA requests comments on whether additional or different 

subcategories should be considered. Comments should include 

detailed information regarding why a new or different 

subcategory is appropriate (based on the available data or 

adequate data submitted with the comment), how EPA should define 

any additional/different subcategories, how EPA should account 

for varied or changing fuel mixtures, and how EPA should use the 

available data to determine the MACT floor for any new or 

different categories.
106

G. How did EPA determine the proposed emission limitations for 

new units?

All standards established pursuant to section 112 of the 

CAA must reflect MACT, the maximum degree of reduction in 

emissions of air pollutants that the Administrator, taking into 

consideration the cost of achieving such emissions reductions, 

and any nonair quality health and environmental impacts and 

energy requirements, determines is achievable for each category. 

The CAA specifies that MACT for new boilers and process heaters 

shall not be less stringent than the emission control that is 

achieved in practice by the best-controlled similar source. 

This minimum level of stringency is the MACT floor for new 

units. However, EPA may not consider costs or other impacts in 

determining the MACT floor. EPA must consider cost, nonair 

quality health and environmental impacts, and energy 

requirements in connection with any standards that are more 

stringent than the MACT floor (beyond-the-floor controls). 

H. How did EPA determine the MACT floor for new units?

Similar to the MACT floor process used for existing units, 

the approach for determining the MACT floor must be based on 

available emissions test data. Using such an approach, we 

calculated the MACT floor for a subcategory of sources by 

ranking the emission test results from units within the 
107

subcategory from lowest to highest to identify the best 

controlled similar source. The MACT floor limits for each of 

the HAP and HAP surrogates (PM, mercury, CO, HCl, and D/F) are 

calculated based on the performance (numerical average) of the 

lowest emitting (best controlled) source for each pollutant in 

each of the subcategories.

The MACT floor limits for new sources were calculated using 

the same formula as was used for existing sources. However, as 

was the case for the existing MACT floor analysis, we determined 

that it was inappropriate to use only this MACT floor approach 

to determine variability and to establish emission limits for 

new boilers and process heaters. The main problem with using 

only the HAP emissions test data is that the data may not 

reflect the variability of fuel-related HAP from the best 

controlled similar source over the long term. Based on our 

current information, fuel-related HAP levels in the various 

fuels can vary significantly over time. The variations in fuelrelated HAP inputs directly translate to a variability of fuelrelated HAP stack emissions.

As previously discussed above, we account for variability

of the best-controlled source in setting floors, not only 

because variability is an element of performance, but because it

is reasonable to assess best performance over time. If we do 
108

not account for this variability, we would expect that even the 

best controlled similar source would potentially exceed the 

floor emission levels a significant part of the time which would 

mean that their variability was not properly accounted for when 

setting the floor. We calculated the MACT floor based on the 

UPL (upper 99th percentile) as described earlier from the 

average performance of the best controlled similar source, 

Students t-factor, and the total variability of the bestcontrolled source.

This approach reasonably ensures that the emission limit 

selected as the MACT floor adequately represents the average 

level of control actually achieved by the best controlled 

similar source, considering ordinary operational variability.

A detailed discussion of the MACT floor methodology is 

presented in the memorandum “MACT Floor Analysis for the 

Industrial, Commercial, and Institutional Boilers and Process 

Heaters National Emission Standards for Hazardous Air 

Pollutants” in the docket.

The approach that we use to calculate the MACT floors for 

new sources is somewhat different from the approach that we use 

to calculate the MACT floors for existing sources. While the 

MACT floors for existing units are intended to reflect the 

performance achieved by the average of the best performing 
109

twelve percent of sources, the MACT floors for new units are 

meant to reflect the emission control that is achieved in 

practice by the best controlled source. Thus, for existing 

units, we are concerned about estimating the central tendency of 

a set of multiple units, while for new units, we are concerned 

about estimating the level of control that is representative of 

that achieved by a single best controlled source. As with the 

analysis for existing sources, the new unit analysis must 

account for variability. To accomplish this for new sources, 

for the fuel dependent HAP emissions, we determined what the 

best controlled source has achieved in light of the inherent and 

unavoidable variations in the HAP content of the fuel that such 

unit might potentially use. For non-fuel dependent HAP 

emissions, on the other hand, we look at the inherent 

variability of the control technology used by the bestcontrolled source in the subcategory. These approaches, 

respectively, represent the most reasonable way to estimate 

performance for purposes of establishing MACT floors for new 

units, given the data available. 

For fuel dependent HAP emissions (mercury and HCl), we 

calculated the variability factor by looking at data on HAP 

variability in fuel obtained through our information collection 

request. We derived the fuel dependent variability factor by 
110

dividing the highest observed HAP concentration by the lowest 

observed HAP concentration from the fuel analyses from the bestcontrolled source. Once we calculated the fuel dependent 

variability factors, we applied these factors to the average 

measured emissions performance of the best controlled similar 

source to derive the MACT floor level of control. This approach 

reasonably estimates the best source’s level of emissions, 

adjusted for unavoidable variation in fuel characteristics which 

have a direct impact on emissions. 

1. Determination of MACT for the Fuel-related HAP

In developing the MACT floor for the fuel-related HAP (PM, 

HCl, and mercury), as described earlier, we are using PM as a 

surrogate for non-mercury metallic HAP and HCl as a surrogate 

for the acid gases. Table 5 presents for each subcategory and 

fuel-related HAP the average emission level of the best 

controlled similar source and the MACT floor (99 percent UPL) 

which includes the variability across the best controlled 

similar source and the long term variability of that source.

Table 5. Summary of MACT Floor Results for the Fuel-Related HAP 

for New Sources. 

Subcategory Parameter PM

Lb/MMBtu

Mercury

Lb/MMBtu

HCl

Lb/MMBtu

Units 

designed 

for Coal 

firing

Avg of top 

performer

0.000396 1.18E-07 3.85E-05
111

99% UPL of 

top (test 

runs) =

0.000928 3.89E-07 5.21E-05

Units 

designed 

for Biomass 

firing 

Avg of top 

performer

0.00216 9.73E-08 7.85E-04

99% UPL of 

top (test 

runs) =

0.00711 1.86E-07 3.07E-03

Units 

designed 

for Liquid 

Fuel firing

Avg of top 

performer 

0.000511 5.87E-08 3.99E-04

99% UPL of 

top (test 

runs) =

0.00154 2.47E-07 9.80E-04

Units 

designed 

for other 

gas firing

Avg of top 

performer 

0.00042 8.25E-08 1.70E-06

99% UPL of 

top (test 

runs) =

0.0024 1.86E-07 2.50E-06

2. Determination of MACT for Organic HAP

In developing the MACT floor for organic HAP, as described 

earlier, we are using CO as a surrogate for non-dioxin organic 

HAP. Table 6 presents for each subcategory and CO and D/F the 

average emission level of the best controlled similar source and 

the MACT floor (99 percent UPL) which includes the variability 

across the best controlled similar source and the long term 

variability of that source.

Table 6. Summary of MACT Floor Results for the Organic HAP for 

New Sources. 
112

Subcategory Parameter CO

(ppm @ 3 

percent 

oxygen)

Dioxin/Furan

(TEQ)

(ng/dscm @ 7 

percent 

oxygen)

Stoker –

Coal

Avg of top 

performer

4.29 0.00152

99% UPL of top% 

(test runs) =

6.53 0.00282

Fluidized 

Bed - Coal

Avg of top 

performer

8.26 9.05E-06

99% UPL of top% 

(test runs) =

39.9* 2.54E-05

PC – Coal Avg of top 

performer

25.0 1.04E-03

99% UPL of top% 

(test runs) =

97.5* 1.47E-03

Stoker –

Biomass

Avg of top 

performer

920 1.52E-05

99% UPL of top% 

(test runs) =

3730* 4.86E-05

Fluidized 

Bed –

Biomass

Avg of top 

performer

25.8 2.27E-03

99% UPL of top% 

(test runs) =

34.2 6.48E-03

Suspension 

Burner/

Dutch Oven

Avg of top 

performer

352 9.52E-03

99% UPL of top% 

(test runs) =

1050* 2.79E-02

Fuel Cell –

Biomass

Avg of top 

performer

110 2.42E-04

99% UPL of top% 

(test runs) =

264* 4.17E-04

Units 

designed 

for Liquid 

fuel firing

Avg of top 

performer

0.125 1.09E-03

99% UPL of top% 

(test runs) =

0.125 1.52E-03

Units 

designed 

for other 

gases 

Avg of top 

performer

0.0129 2.67E-03
113

firing

99% UPL of top% 

(test runs) =

0.0129 8.28E-03

*Value is higher than existing floor limit in the same 

subcategory. Therefore defaulted to existing floor limit for 

the same subcategory.

For organic HAP, as previously discussed above for the 

fuel-related, we account for variability in setting floors, not 

only because variability is an element of performance, but 

because it is reasonable to assess best performance over time. 

Here, we know that CO (as a surrogate for non-dioxin organic 

HAP) emissions does not vary significantly over the operating 

range of the unit. Thus, we have not added any additional 

operational variability to account for operation at lower 

capacity rates. 

We are proposing a work practice standard under section 

112(h) that would require an annual tune-up for new boilers and 

process heaters combusting natural gas or refinery gas. These 

boilers and process heaters are units included in the Gas 1 and 

metal processing furnace subcategories. We are specifically 

seeking comment on whether the application of measurement 

methodology to sources in this subcategory is impracticable due 

to technological or economic limitations, as specified in 

section 112(h)(2)(B).
114

This proposal for new boilers and process heaters 

combusting natural gas or refinery gas is based on the same 

reasons discussed previously for existing boilers and process 

heaters combusting natural gas or refinery gas. That is, we 

believe that proposing emission standards for new gas-fired 

boilers and process heaters that result in the need to employ 

the same emission control system as needed for the other fuel 

types would have the negative benefit of providing a 

disincentive for switching to gas as a control technique (and a 

pollution prevention technique) for boilers and process heaters 

in the other fuel subcategories. In addition, emission limits 

on gas-fired boilers and process heaters may have the negative 

benefit of providing an incentive for a facility to switch from 

gas (considered a “clean” fuel) to a “dirtier” but cheaper fuel 

(i.e., coal). It would be inconsistent with the emissions 

reductions goals of the CAA, and of section 112 in particular, 

to adopt requirements that would result in an overall increase 

in HAP emissions. We are soliciting comment on the extent to 

which new facilities would be expected to switch away from 

natural gas to a “dirtier” fuel if emissions limits for new such 

facilities are adopted.

Thus, a work practice, as discussed above for existing 

boilers and process heaters combusting natural gas or refinery 
115

gas, is being proposed to limit the emission of HAP for new 

natural gas-fired and refinery gas-fired boilers and process 

heaters.

We request comments on whether the emission limits listed 

in Table 7 of this preamble for new units in the Gas 1 and Metal 

Process Furnace subcategories should be promulgated. Comments 

should include detailed information regarding why emission 

limits for these gas-fired boilers and process heaters are 

appropriate.

Table 7. Summary of MACT Floor Results for New Units in the Gas 

1 and Metal Process Furnace Subcategories.

Subcate

gory

Parame

ter

PM

Lb/MMB

tu

Mercury

Lb/MMBt

u

HCl

LB/MMB

tu

CO

(ppm @ 

3 

percent 

oxygen)

Dioxin/Furan

(Total TEQ)

(ng/dscm @ 

7 percent 

oxygen)

Units 

designe

d for 

NG/RG 

firing

Avg of 

top 

perfor

mer 

0.0001

3

9.4E-08 7.3E050.013 0.0026

99% 

UPL of 

top 

(test 

runs) 

=

0.0005 2.0E-07 0.0002 20 0.01

Metal 

Process

Furnace

s

Avg of 

top 

perfor

mer 

0.0065 3.3E-08 8.6E050.5 0.0026

99% 0.02 2.0E-07 0.0002 2 0.004
116

I. How did EPA consider beyond-the-floor for new units?

The MACT floor level of control for new units is based on 

the emission control that is achieved in practice by the best 

controlled similar source within each of the subcategories. No 

technologies were identified that would achieve HAP reduction 

greater than the new source floors for the subcategories. 

Fuel switching to natural gas is a potential regulatory 

option beyond the new source floor level of control that would 

reduce HAP emissions from non-gas-fired units. However, based 

on current trends within the industry, EPA projects that the 

majority of new boilers and process heaters will be built to 

fire natural gas as opposed to solid and liquid fuels such that 

the overall emissions reductions associated with this option 

would be minimal. In addition, natural gas supplies are not 

available in some areas, and supplies to industrial customers 

can be limited during periods when natural gas demand exceeds 

supply. Thus, this potential control option may be unavailable 

to many sources in practice. Limited emissions reductions in 

combination with the high cost of fuel switching and 

UPL of 

top 

(test 

runs) 

=
117

considerations about the availability and technical feasibility 

of fuel switching makes this an unreasonable regulatory option 

that was not considered further.7

An energy assessment is a beyond-the-floor standard being 

proposed for existing facilities. However, we are not proposing 

it as a beyond-the-floor option for new major source facilities 

since we believe it would not be cost effective because most 

projected new boilers or process heaters will be installed at 

existing major source facility which would have already 

conducted a energy assessment as required by this proposed rule. 

We also believe that any new greenfield major source facility 

having boilers or process heaters will be designed to operate 

with energy efficiency. 

 Nonair quality health, 

environmental impacts, and energy effects were not significant 

factors. No beyond-the-floor options for gas-fired boilers were 

identified. 

Based on the analysis discussed above, EPA decided to not 

go beyond the MACT floor level of control for new sources in 

this proposed rule. A detailed description of the beyond-thefloor consideration is in the memorandum “Methodology for 

Estimating Cost and Emissions Impacts for Industrial, 

 

7 Memorandum “Development (2010) of Fuel Switching Costs and Emission Reductions for Industrial, Commercial, 

and Institutional Boilers and Process Heaters National Emission Standards for Hazardous Air Pollutants,” April 

2010.
118

Commercial, Institutional Boilers and Process Heaters National 

Emission Standards for Hazardous Air Pollutants” in the docket.

J. What other compliance alternatives were considered?

CAA section 112(d)(4) allows the Administrator to set a 

health-based standard for a limited set of HAP: “pollutants for 

which a health threshold has been established.” EPA may

consider that threshold, with an ample margin of safety, in 

establishing standards under CAA section 112(d). In the 2007

rule, EPA took the position that HCl and manganese were both 

“health threshold pollutants” and relied on section 112(d)(4) in 

deciding to establish alternative standards for HCl and 

manganese. 69 FR at 55239–44. In today’s proposed action, we 

considered whether to propose the health-based compliance 

alternatives that were part of the vacated Boiler MACT standard. 

As noted in the proposal of the MACT II chemical recovery 

combustion sources (63 FR 18755; April 15, 1998), “use of

section 112(d)(4) authority is wholly discretionary . . .[C]ases 

may arise in which . . . considerations dictate that the Agency 

should not invoke this authority to establish less stringent 

standards, despite the existence of a health effects threshold 

that is not jeopardized.” We further stated in that rule that 

“in considering appropriate uses of its discretionary authority 

under section 112(d)(4), EPA intends to consider other factors 
119

in addition to health thresholds, including uncertainty and 

potential’ adverse environmental effects,’ as that phrase is 

defined in section 1 12(a)(7).”

Thus while we have discretion to set a health-based 

standard under section 112(d)(4) where we believe a pollutant 

has an established health threshold, that discretion must be 

exercised reasonably. As explained further below, we do not 

believe that establishing a threshold level would provide an 

“ample margin of safety,” as required by section 112(d)(4), and 

therefore are not proposing to relax the stringency of the 

emission standard for HCl using the section 112(d)(4) in this 

case. 

We are not proposing health-based compliance alternatives 

here for three primary reasons. First, while the CAA allows the 

Administrator to consider a health-based standard, such a 

standard must be robust enough to allow her to ensure that an 

ample margin of safety has been provided. Second, since HCl is 

used as a surrogate for other HAP acid gases hydrogen fluoride 

and hydrogen cyanide, she must consider whether such a strategy 

would necessitate setting additional MACT standards for these 

gases for which HCl was being used as a surrogate. And third, 

since the decision to propose health-based standards is 
120

discretionary, consideration can and should be given to all the 

direct effects that result from controlling HCl emissions.

First, the classification of HCl as a threshold pollutant 

is based on only one animal study, and no human data are

available for review (63 FR 18755) – clearly not sufficient to 

ensure protection with adequate margin of safety. Second, it is 

clear that hydrogen chloride (HCl) is a respiratory toxic

pollutant; that is, it can cause irritation in the nose, throat, 

and upper respiratory tract which could ultimately lead to 

chronic damage. This is also true of the HAPs hydrogen fluoride 

(HF) and hydrogen cyanide (HCN), the other acid gas HAPs that 

may be emitted by coal-fired boilers which can be controlled via 

the same technologies, and for which EPA must issue standards in

this rulemaking. The respiratory toxicity of HCl is generally 

considered not to occur at chronic exposure concentrations below 

the reference concentration, or RfC, which is 20 ug/m3. 

However, the determination of this reference concentration does 

not consider the potential for simultaneous exposures to other 

respiratory toxicants. In addition, HCl is corrosive to the 

eyes, skin, and mucous membranes. Acute inhalation exposure may 

cause eye, nose, and respiratory tract irritation and 

inflammation and pulmonary edema in humans. Chronic 

occupational exposure to hydrochloric acid has been reported to 
121

cause gastritis, bronchitis, and dermatitis in workers. 

Prolonged exposure to low concentrations may also cause dental 

discoloration and erosion. No information is available on the 

reproductive or developmental effects of hydrochloric acid in 

humans. In rats exposed to hydrochloric acid by inhalation, 

altered estrus cycles have been reported in females and 

increased fetal mortality and decreased fetal weight have been 

reported in offspring. EPA has not classified hydrochloric acid 

for carcinogenicity. The inhalation of HCl has also been known 

to lead to chemical-induced asthma in some cases. As such, its 

effects can be manifested when it is inhaled in combination with 

other asthma-inducing pollutants (e.g., ozone, formaldehyde, or 

acrolein), triggering asthma attacks, even at concentration 

levels well below its RfC. Since boilers are often located at 

industrial sites where other pollutants are emitted, it would be 

reasonable to consider the boiler emissions in conjunction with 

other emissions at the same site, particularly since such sites 

are often found in polluted urban areas as well as in polluted 

urban areas. At a minimum, it would be reasonable to consider 

the combination of all respiratory toxicants and asthmaexacerbating pollutants in the ambient air near boilers when 

estimating their potential impacts to the human respiratory 

system, and when considering the adoption of HCl emission 
122

standards less stringent than the MACT approach would dictate, 

in light of the fact that there can be significant pollutant 

emissions from other emissions points at industrial sites where 

boilers are located. Since EPA cannot quantify with sufficient 

certainty the potential health effects of this complex mixture 

of pollutants at every industrial site in the country at which 

a boiler is located, we are choosing to err on the side of 

protecting public health by not proposing to use the discretion 

offered by section 112(d)(4). 

We further note that there are other adverse environmental 

effects of HCl emissions from boilers. When HCl gas encounters 

water in the atmosphere, it forms hydrochloric acid, which can 

contribute to further aquatic and terrestrial acidification, 

ecological impacts that are already causing environmental 

degradation in many areas of the country. Similarly, when HF 

gas encounters water in the atmosphere, it forms hydrofluoric 

acid. We believe that it is reasonable for EPA to decide not to 

use its discretion under section 112(d)(4) to weaken the 

emission standard for HCl (and in turn for HF) from boilers, 

adding to this environmental burden, when it is simultaneously 

investigating ways to reduce environmental degradation from 

acidification (i.e., EPA is currently considering the adoption 
123

of tighter ambient standards for oxides of sulfur (SOx) and 

oxides of nitrogen (NOx) to reduce environmental acidification).

Lastly, setting MACT standards for HCl (as a surrogate for 

the other HAP acid gases hydrogen fluoride and hydrogen cyanide) 

and PM (as a surrogate for metals including manganese) is 

anticipated to result in significant control for other 

pollutants emitted, most notably SO2 and other non-HAP acid gases 

(e.g., hydrogen bromide), along with condensable PM and will 

likely provide additional control for mercury and other HAP 

metals (e.g., selenium). The additional reductions of SO2 alone 

attributable to the proposed MACT standard for HCl are estimated 

to be 400,000 tons per year in the third year following 

promulgation of the HCl standard. These are substantial 

reductions with substantial public health benefits. Although 

MACT standards may only address HAP, not criteria pollutants, 

Congress fully expected MACT standards to have the collateral 

benefit of controlling criteria pollutants as well, and viewed 

this as an important benefit of the air toxics program.8

 

8 See S. Rep. No. 101-228, 101st Cong. 1st sess. At 172

 It, 

therefore, is appropriate that EPA consider such benefits as a 

factor in determining whether to exercise its discretionary CAA 

section 112 (d)(4) authority.
124

Although we are not proposing this approach for the 

reasons discussed above, we request comment on a health-based 

compliance alternative for HCl and/or manganese and other 

information on HCl and manganese health and environmental 

effects we should consider. Commenters should also address the 

issue of other environmental benefits which might result from 

control of HCl and manganese at MACT levels, including control 

of other acid gases and metals and control of secondary PM 

(i.e., PM condensing from acid gases). We will consider these 

comments in making an ultimate determination as to whether to 

adopt a health-based compliance alternatives for HCl or

manganese.

K. How did we select the compliance requirements?

We are proposing testing, monitoring, notification, and 

recordkeeping requirements that are adequate to assure 

continuous compliance with the requirement of this proposed

rule. These requirements are described in detail in sections 

IV.K to IV.N. We selected these requirements based upon our 

determination of the information necessary to ensure that the 

emission standards and work practices are being followed and 

that emission control devices and equipment are maintained and 

operated properly. These proposed requirements ensure 

compliance with this proposed rule without imposing a 
125

significant additional burden for facilities that must implement 

them.

We are proposing that compliance with the emission limits 

for PM, HCl, mercury, CO, and D/F be demonstrated by an initial 

performance test. To ensure continuous compliance with the 

proposed PM, HCl, and mercury emission limits, this proposed 

rule would require continuous parameter monitoring of control 

devices and recordkeeping. Additionally, this proposed rule 

would require annual performance tests to ensure, on an ongoing 

basis, that the air pollution control device is operating 

properly and its performance has not deteriorated. If initial 

compliance with the mercury and/or HCl emission limits are

demonstrated by a fuel analysis performance test, this proposed 

rule would require fuel analyses monthly, with compliance 

determined based on an annual average.

We evaluated the feasibility and cost of applying PM CEMS 

to boilers and process heaters. CEMS have been used in Europe 

to monitor PM emissions from a variety of industrial sources. 

Several electric utility companies in the United States have now 

installed or are planning to install PM CEMS. In recognition of 

the fact that PM CEMS are commercially available, EPA developed 

and promulgated Performance Specifications (PS) for PM CEMS (69 

FR 1786, January 12, 2004). PS for PM CEMS are established 
126

under PS-11 in appendix B to 40 CFR part 60 for evaluating the 

acceptability of a PM CEM used for determining compliance with 

the emission standards on a continuous basis. For PM CEM 

monitoring, capital costs were estimated to be $88,000 per unit 

and annualized costs were estimated to be $33,000 per unit. We 

determined that requiring PM CEMS for units with heat input 

capacity greater or equal to 250 MMBtu/hr and combusting either 

coal, biomass, or oil is a reasonable monitoring option. We are 

requesting comment on the application of PM CEMS to boilers and 

process heaters, and the use of data from such systems for 

compliance determinations under this proposed rule.

We reviewed cost information for CO CEMS to make the 

determination on whether to require CO CEMS or conducting annual 

THC testing to demonstrate continuous compliance with the THC

emission limit. In evaluating the available cost information, 

we determined that requiring CO CEMS for units with heat input 

capacities greater or equal to 100 MMBtu/hr is reasonable. This

proposed rule would require units with heat input capacities 

less than 100 MMBtu/hr to conduct initial and annual performance 

(stack) tests. 

The majority of test methods that this proposed rule would 

require for the performance stack tests have been required under 

many other EPA standards. The only applicable voluntary 
127

consensus standard identified is ASTM Method D6784-02 (Ontario 

Hydro). The majority of emissions tests upon which the proposed 

emission limits are based were conducted using these test 

methods.

When a performance test is conducted, we are proposing that 

parameter operating limits be determined during the tests. 

Performance tests to demonstrate compliance with any applicable 

emission limits are either stack tests or fuel analysis or a 

combination of both.

To ensure continuous compliance with the proposed emission 

limits and/or operating limits, this proposed rule would require 

continuous parameter monitoring of control devices and 

recordkeeping. We selected the following requirements based on 

reasonable cost, ease of execution, and usefulness of the 

resulting data to both the owners or operators and EPA for 

ensuring continuous compliance with the emission limits and/or 

operating limits.

We are proposing that certain parameters be continuously 

monitored for the types of control devices commonly used in the 

industry. These parameters include opacity monitoring except 

for wet scrubbers; pH, pressure drop and liquid flowrate for wet 

scrubbers; and sorbent injection rate for dry scrubbers. You 

must also install a bag leak detection system for fabric 
128

filters. If you cannot monitor opacity for control systems with 

an ESP then you must monitor the secondary current and voltage 

or total power input for the ESP. These monitoring parameters 

have been used in other standards for similar industries. The 

values of these parameters are established during the initial or 

most recent performance test that demonstrates compliance. 

These values are your operating limits for the control device.

You would be required to set parameters based on 4-hour 

block averages during the compliance test, and demonstrate 

continuous compliance by monitoring 12-hour block average values 

for most parameters. We selected this averaging period to 

reflect operating conditions during the performance test to 

ensure the control system is continuously operating at the same 

or better level as during a performance test demonstrating 

compliance with the emission limits.

To demonstrate continuous compliance with the emission and 

operating limits, you would also need daily records of the 

quantity, type, and origin of each fuel burned and hours of 

operation of the affected source. If you are complying with the 

chlorine fuel input option, you must keep records of the 

calculations supporting your determination of the chlorine 

content in the fuel.
129

If a source elected to demonstrate compliance with the HCl

or mercury limit by using fuel which has a statistically lower 

pollutant content than the emission limit, we are proposing that 

the source’s operating limit is the emission limit of the 

applicable pollutant. Under this option, a source is not 

required to conduct performance stack tests. If a source

demonstrates compliance with the HCl or mercury limit by using 

fuel with a statistically higher pollutant content than the 

applicable emission limit, but performance tests demonstrate 

that the source can meet the emission limits, then the source’s 

operating limits are the operating limits of the control device 

(if used) and the fuel pollutant content of the fuel 

type/mixture burned.

This proposed rule would specify the testing methodology 

and procedures and the initial and continuous compliance

requirements to be used when complying with the fuel analysis

options. Fuel analysis tests for total chloride, gross 

calorific value, mercury, sample collection, and sample 

preparation are included in this proposed rule.

If you elect to comply based on fuel analysis, you will be

required to statistically analyze, using the z-test, the data to

determine the 90th percentile confidence level. It is the 90th

percentile confidence level that is required to be used to 
130

determine compliance with the applicable emission limit. The 

statistical approach is required to assist in ensuring

continuous compliance by statistically accounting for the 

inherent variability in the fuel type.

We are proposing that a source be required to recalculate 

the fuel pollutant content only if it burns a new fuel type or 

fuel mixture and conduct another performance test if the results 

of recalculating the fuel pollutant content are higher than the 

level established during the initial performance test.

For boilers and process heaters with heat input capacities 

greater or equal to 100 MMBtu/hr, we are proposing that CO be 

continuously monitored to demonstrate that average CO emissions, 

on a 30-day rolling average, are at or below the proposed CO

limit.

For boilers and process heaters with heat input capacities 

between 10 and 100 MMBtu/hr, we are proposing that a performance 

stack test of CO emissions be conducted to demonstrate 

compliance with the CO emission limit.

L. What alternative compliance provisions are being proposed?

We are proposing that owners and operators of existing 

affected sources may demonstrate compliance by emissions 

averaging for units at the affected source that are within a 

single subcategory.
131

As part of the EPA’s general policy of encouraging the use 

of flexible compliance approaches where they can be properly 

monitored and enforced, we are including emissions averaging in

this proposed rule. Emissions averaging can provide sources the 

flexibility to comply in the least costly manner while still

maintaining regulation that is workable and enforceable. 

Emissions averaging would not be applicable to new sources and 

could only be used between boilers and process heaters in the 

same subcategory at a particular affected source. Also, owners 

or operators of existing sources subject to the Industrial 

Boiler NSPS (40 CFR part 60, subparts Db and Dc) would be

required to continue to meet the PM emission standard of that 

NSPS regardless of whether or not they are using emissions 

averaging.

Emissions averaging would allow owners and operators of an 

affected source to demonstrate that the source complies with the 

proposed emissions limits by averaging the emissions from an 

individual affected unit that is emitting above the proposed

emission limits with other affected units at the same facility 

that are emitting below the proposed emission limits.

This proposed rule includes an emissions averaging 

compliance alternative because emissions averaging represents an 

equivalent, more flexible, and less costly alternative to 
132

controlling certain emission points to MACT levels. We have 

concluded that a limited form of averaging could be implemented 

that would not lessen the stringency of the MACT floor limits 

and would provide flexibility in compliance, cost and energy 

savings to owners and operators. We also recognize that we must 

ensure that any emissions averaging option can be implemented

and enforced, will be clear to sources, and most importantly, 

will be no less stringent than unit by unit implementation of 

the MACT floor limits.

EPA has concluded that it is permissible to establish 

within a NESHAP a unified compliance regimen that permits

averaging within an affected source across individual affected 

units subject to the standard under certain conditions. 

Averaging across affected units is permitted only if it can be 

demonstrated that the total quantity of any particular HAP that 

may be emitted by that portion of a contiguous major source that 

is subject to the NESHAP will not be greater under the averaging 

mechanism than it could be if each individual affected unit 

complied separately with the applicable standard. Under this

test, the practical outcome of averaging is equivalent to 

compliance with the MACT floor limits by each discrete unit, and

the statutory requirement that the MACT standard reflect the 
133

maximum achievable emissions reductions is, therefore, fully 

effectuated.

In past rulemakings, EPA has generally imposed certain 

limits on the scope and nature of emissions averaging programs. 

These limits include: (1) No averaging between different types 

of pollutants, (2) no averaging between sources that are not

part of the same affected source, (3) no averaging between 

individual sources within a single major source if the 

individual sources are not subject to the same NESHAP, and (4) 

no averaging between existing sources and new sources.

This proposed rule would fully satisfy each of these 

criteria. First, emissions averaging would only be permitted 

between individual sources at a single existing affected source, 

and would only be permitted between individual sources subject 

to the boiler and process heater NESHAP. Further, emissions 

averaging would not be permitted between two or more different 

affected sources. Finally, new sources could not use emissions 

averaging. Accordingly, we have concluded that the averaging of

emissions across affected units is consistent with the CAA. In 

addition, the proposed rule would require each facility that 

intends to utilize emission averaging to submit an emission

averaging plan, which provides additional assurance that the 

necessary criteria will be followed. In this emission averaging 
134

plan, the facility must include the identification of (1) all

units in the averaging group, (2) the control technology 

installed, (3) the process parameter that will be monitored, (4) 

the specific control technology or pollution prevention measure 

to be used, (5) the test plan for the measurement of the HAP 

being averaged, and (6) the operating parameters to be monitored 

for each control device. Upon receipt, the regulatory authority 

would not be able to approve an emission averaging plan

containing averaging between emissions of different types of 

pollutants or between sources in different subcategories.

This proposed rule would also exclude new affected sources 

from the emissions averaging provision. EPA believes emissions 

averaging is not appropriate for new sources because it is most 

cost effective to integrate state-of-the-art controls into 

equipment design and to install the technology during 

construction of new sources. One reason we allow emissions 

averaging is to give existing sources flexibility to achieve 

compliance at diverse points with varying degrees of add-on 

control already in place in the most cost-effective and 

technically reasonable fashion. This flexibility is not needed 

for new sources because they can be designed and constructed 

with compliance in mind.
135

With concern about the equivalency of emissions reductions 

from averaging and non-averaging in mind, we are also proposing

under the emission averaging provision caps on the current 

emissions from each of the sources in the averaging group. The

emissions for each unit in the averaging group would be capped 

at the emission level being achieved on the effective date of 

the final rule. These caps would ensure that emissions do not 

increase above the emission levels that sources currently are 

designed, operated, and maintained to achieve. In the absence 

of performance tests, in documenting these caps, these sources 

will document the type, design, and operating specification of 

control devices installed on the effective date of the final 

rule to ensure that existing controls are not removed or lessen. 

By including this provision in this proposed rule, we would 

further ensure that emission averaging results in environmental 

benefits equivalent or better over what would have happened

without emission averaging.

In addition, we are proposing that a discount factor of ten 

percent would be applied when emissions averaging is used. This 

discount factor will further ensure that averaging will be at 

least as stringent as the MACT floor limits in the absence of 

averaging. The emissions averaging provision would not apply to 

individual units if the unit shares a common stack with units in 
136

other subcategories, because in that circumstance it is not 

possible to distinguish the emissions from each individual unit.

M. How did EPA determine compliance times for the proposed 

rule?

Section 112 of the CAA specifies the dates by which 

affected sources must comply with the emission standards. New 

or reconstructed units must be in compliance with this proposed 

rule immediately upon startup or [DATE THE FINAL RULE IS 

PUBLISHED IN THE FEDERAL REGISTER], whichever is later. 

Existing sources are allowed 3 years to comply with the final 

rule. This is the maximum period allowed by the CAA. We 

believe that 3 years for compliance is necessary to allow 

adequate time to design, install and test control systems that 

will be retrofitted onto existing boilers, as well as obtain 

permits for the use of add-on controls.

N. How did EPA determine the required records and reports for 

this proposed rule?

You would be required to comply with the applicable 

requirements in the NESHAP General Provisions, subpart A of 40 

CFR part 63, as described in Table 10 of the proposed subpart 

DDDDD. We evaluated the General Provisions requirements and 

included those we determined to be the minimum notification, 
137

recordkeeping, and reporting necessary to ensure compliance 

with, and effective enforcement of, this proposed rule. 

We are also requiring that you keep daily records of the 

total fuel use by each affected source, subject to an emission 

limit or work practice standard, along with a description of the 

fuel, the total fuel usage amounts and units of measure, and 

information on the supplier and original source of the fuel. 

This information is necessary to ensure that the affected source 

is complying with the emission limits from the correct 

subcategory.

We would require additional recordkeeping if you chose to 

comply with the chlorine or mercury fuel input option. You 

would need to keep records of the calculations and supporting 

information used to develop the chlorine or mercury fuel input 

operating limit.

O. How does this proposed rule affect permits?

The CAA requires that sources subject to this proposed rule 

be operated pursuant to a permit issued under EPA-approved State 

operating permit program. The operating permit programs are 

developed under title V of the CAA and the implementing 

regulations under 40 CFR parts 70 and 71. If you are operating 

in the first 3 years of your operating permit, you will need to 

obtain a revised permit to incorporate this proposed rule. If 
138

you are in the last 2 years of your operating permit, you will 

need to incorporate this proposed rule into the next renewal of 

your permit.

P. Alternate Standard for Consideration

As discussed above, EPA is proposing a definition of nonhazardous solid waste under RCRA in a concurrent notice. The 

proposed CAA section 112(d) standards for boilers and process 

heaters are based on that proposed definition of solid waste. 

Therefore, the emission limits presented in Tables 1 through 5

above are based on subcategories established considering sources 

that are ICI boilers and process heaters under the proposed 

definition of solid waste under RCRA. However, the RCRA

proposal also identifies and solicits comment on an alternative 

approach for defining solid waste, under which more units would 

be considered solid waste incineration units than under the 

proposed definition. As such, the alternative approach for 

defining solid waste under RCRA would result in a different, 

smaller population of units being covered by Boiler MACT. 

Consistent with EPA’s solicitation of comment on an alternative 

proposed definition of solid waste under RCRA, we calculated 

MACT floors using emission rates for units that would be ICI 

boilers and process heaters under that alternative definition, 

using the same statistical procedures described above. Table 6
139

reflects that calculation of MACT floor limits for the existing 

source subcategories that would be changed by the alternative 

definition of solid waste identified in the concurrent RCRA 

proposal, compared to the proposed definition of solid waste in 

that proposal. The MACT floor limits for the remaining existing 

source subcategories (Gas 1, Gas 2, and Liquid) would not change 

under the alternative definition of solid waste on which EPA is 

soliciting comment in the concurrent RCRA proposal, and are 

therefore not included in Table 8 because the MACT floor limits 

for those subcategories would be the same under the alternative 

definition of solid waste as under the proposed definition

TABLE 8. EXISTING MACT FLOOR LIMITS USING THE “ALTERNATIVE 

APPROACH” UNDER CONSIDERATION AND COMMENT IN THE CONCURRENTLY 

PROPOSED RCRA RULE

(pounds per million British thermal units)

Subcategory Particulate 

Matter (PM)

Hydrogen 

Chloride 

(HCl)

Mercury

(Hg)

Carbon 

Monoxide(CO)

(ppm

@3%oxygen)

Dioxins/

Furans

(Total TEQ)

(ng/dscm) @ 7%O2

Existing –

Coal Stoker 

0.02 0.008 0.000003 30 0.0029

Existing -

Coal 

Fluidized 

Bed

0.02 0.008 0.000003 40 0.0073

Existing –

Pulverized 

Coal

0.02 0.008 0.000003 70 0.0038

Existing –

Biomass 

Stoker 

0.02 0.03 0.000000

4

540 0.000049

Existing -

Biomass 

0.02 0.03 0.000000 10,650 0.093
140

Fluidized 

Bed

4

Existing –

Biomass 

Suspension

Burner/Dutc

h Oven

0.02 0.03 0.000000

4

1,430 0.61

Existing –

Biomass 

Fuel Cells

0.02 0.03 0.000000

4

460 0.062

Comparing the emissions limits in Table 1 (based on the 

proposed definition of solid waste) with those in Table 8 (based 

on the alternative definition of solid waste), the MACT emission 

limits for PM and mercury for the biomass subcategories would be 

less stringent if they are based on the alternative definition 

of solid waste while the HCl emission limits for the coal and 

biomass subcategories would be more stringent if they are based 

on the alternative definition.

The potential emissions reductions if the MACT floor limits 

are calculated based on the alternative definition of solid 

waste would be generally lower than the potential emissions 

reductions for MACT floors based on the proposed definition of 

solid waste, because 281 fewer boilers and process heaters would 

be subject to the boiler and process heater MACT standards under 

the alternative definition. These units would instead be 

considered CISWI units under the alternative definition of solid 

waste. For example, mercury emissions reduction would be 17 
141

tons per year based on the alternative definition of solid waste 

(compared to 19 tons per year based on the proposed definition) 

and HCl emissions reduction would be 44,000 tons per year based 

on the alternative definition (compared to 47,000 tons per year 

based on the proposed definition). Most (181) of the 281 units 

that would be considered CISWI units under the alternative 

definition of solid waste proposed under RCRA are biomass-fired 

boilers or process heaters, with the others being in the coal 

and liquid fuel subcategories. 

The resulting total national cost impact of the proposed 

emission limits based on the alternative definition of solid 

waste would be 11.3 billion dollars in capital expenditures and 

4.3 billion dollars per year in total annual costs. This 

compares to $13.5 billion in capital costs and $5.4 billion in 

annual costs under the proposed definition of solid waste in the 

RCRA proposed rule. Table 9 of this preamble shows the capital 

and annual cost impacts for each subcategory under the 

alternative definition of solid waste. Costs include testing 

and monitoring costs, but not recordkeeping and reporting costs.

TABLE 9. SUMMARY OF CAPITAL AND ANNUAL COSTS FOR 

EXISTING SOURCES UNDER THE ALTERNATIVE SOLID WASTE DEFINITION

Source Subcategory Estimated/

Projected 

No. of 

Affected 

Units

Capital 

Costs 

(106$)

Annualized 

Cost 

(106$/yr)
142

Existing 

Units

Coal units 524 3,850 1,484

Biomass 

units

239 1,324 359

Liquid 

units

796 2,153 658

Gas (NG/RG) 

units

11,402 2,674 1,399

Gas (other) 

units

193 1,298 387

Energy 

Audit

ALL 1,550 

facilities

24.9

A discussion of the methodology used to estimate cost 

impacts is presented in “Methodology and Results of Estimating 

the Cost of Complying with the Industrial, Commercial, and 

Institutional Boiler and Process Heater NESHAP (2010)” in the 

Docket.

We are soliciting public comments on the emission limits 

listed in Table 6 of this preamble, consistent with EPA’s 

solicitation of comments on the alternative definition of solid 

waste concurrently proposed under RCRA. As explained above, the 

MACT floor limits proposed today are based on the proposed 

definition of solid waste under RCRA. However, because EPA is 

seeking comment on an alternative definition of solid waste 

under RCRA, the Agency believes it is necessary to also solicit 

comment on what the MACT floor limits would be based on the 

universe of sources that would be subject to the boiler and 
143

process heater MACT under that alternative definition. 

V. Impacts of the Proposed Rule

A. What are the air impacts?

Table 10 of this preamble illustrates, for each basic fuel 

subcategory, the emissions reductions achieved by the proposed 

rule (i.e., the difference in emissions between a boiler or 

process heater controlled to the floor level of control and 

boilers or process heaters at the current baseline) for new and 

existing sources. Nationwide emissions of selected HAP (i.e., 

HCl, HF, mercury, metals, and VOC) will be reduced by 48,600

tons per year for existing units and 15 tons per year for new 

units. Emissions of HCl will be reduced by 42,400 tons per year 

for existing units and 9 tons per year for new units. Emissions 

of mercury will be reduced by 8 tons per year for existing units 

and 2.6 pounds per year for new units. Emissions of filterable 

PM will be reduced by 50,100 tons per year for existing units 

and 130 tons per year for new units. Emissions of non-mercury 

metals (i.e., antimony, arsenic, beryllium, cadmium, chromium, 

cobalt, lead, manganese, nickel, and selenium) will be reduced 

by 3,200 tons per year for existing units and will be reduced by 

0.6 ton per year for new units. In addition, emissions of SO2

are established to be reduced by 360,000 tons per year for 

existing sources and 500 tons per year for new sources. 
144

Emissions of dioxin/furans, on a total mass basis, will be 

reduced by 722 grams per year for existing units and 1 gram per 

year for new units. A discussion of the methodology used to 

estimate emissions and emissions reductions is presented in 

“Estimation of Baseline Emissions and Emissions Reductions for 

Industrial, Commercial, and Institutional Boilers and Process 

Heaters (2010)” in the docket.

TABLE 10. SUMMARY OF EMISSIONS REDUCTIONS FOR EXISTING AND NEW 

SOURCES (TONS/YR)b

Source Subcategory HCl PM Non 

Mercury 

Metalsa

Mercury

VOC

Existing 

Units

Coal units 40,700 17,000 770 7 470

Biomass 

units

520 22,500 230 0.2 760

Liquid units 950 10,400 2,200 0.00005 290

Gas 1 

(NG/RG) 

units

9 130 1.1 0.4 72

Gas 2 

(other)units

220 0 0 0.2 170

New 

Units

Coal units 0 0 0 0 0

Biomass 

units

0 0 0 0 0

Liquid units 9 130 0.6 0 3

Gas 1 units 0 0 0 0 0

Gas 2 units 1 4 0.01 0 1

a Includes antimony, arsenic, beryllium, cadmium, chromium, 

cobalt, lead, manganese, nickel, and selenium.
145

B. What are the water and solid waste impacts?

The EPA estimated the additional water usage that would 

result from installing wet scrubbers to meet the emission limits 

for HCl would be 2,800 million gallons per year for existing 

sources and 200,000 gallons per year for new sources. In 

addition to the increased water usage, an additional 842 million 

gallons per year of wastewater would be produced for existing 

sources and 140,000 gallons per year for new sources. The 

annual costs of treating the additional wastewater are $4.6

million for existing sources and $774 for new sources. These 

costs are accounted for in the control costs estimates.

The EPA estimated the additional solid waste that would 

result from the MACT floor level of control to be 81,000 tons 

per year for existing sources and 149,800 tons per year for new 

sources. Solid waste is generated from flyash and dust captured 

in PM and mercury controls as well as from spent carbon that is 

injected into exhaust streams or used to filter gas streams. The 

costs of handling the additional solid waste generated are $3.4

million for existing sources and $6.3 million for new sources. 

These costs are also accounted for in the control costs 

estimates.

A discussion of the methodology used to estimate impacts is 

presented in “Estimation of Impacts for Industrial, Commercial, 
146

and Institutional Boilers and Process Heaters NESHAP (2010)” in 

the Docket.

C. What are the energy impacts?

The EPA expects an increase of approximately 3,160 million 

kilowatt hours (kWh) in national annual energy usage as a result 

of the proposed rule. Of this amount, 3,149 million kWh would 

be from existing sources and 11 million kWh are estimated from 

new sources. The increase results from the electricity required 

to operate control devices, such as wet scrubbers, electrostatic 

precipitators, and fabric filters which are expected to be 

installed to meet the proposed rule. Additionally, the EPA 

expects work practice standards such as boilers tune-ups and 

combustion controls will improve the efficiency of boilers, 

resulting in an estimated fuel savings of 42 trillion BTU each 

year from existing sources and an additional 100,000 million BTU 

each year. This fuel savings estimates includes only those fuel 

savings resulting from gas, liquid, and coal fuels and it is 

based on the assumption that the work practice standards will 

achieve 1% improvement in efficiency.

D. What are the control costs?

To estimate the national cost impacts of the proposed rule 

for existing sources, we developed average baseline emission 

factors for each fuel type/control device combination based on 
147

the emission data obtained and contained in the Boiler MACT 

emission database. If a unit reported emission data, we 

assigned its unit-specific emission data as its baseline 

emissions. For units that did not report emission data, we

assigned the appropriate emission factors to each existing unit 

in the inventory database, based on the average emission factors 

for boilers with similar fuel, design, control devices. We then 

compared each unit’s baseline emission factors to the proposed

MACT floor emission limit to determine if control devices were 

needed to meet the emission limits. The control analysis 

considered fabric filters, carbon bed adsorbers, and activated 

carbon injection to be the primary control devices for mercury 

control, electrostatic precipitators for units meeting mercury 

limits but requiring additional control to meet the PM limits, 

wet scrubbers to meet the HCl limits, tune-ups, replacement 

burners, and combustion controls for CO and organic HAP control, 

and carbon injection for dioxin/furan control. We identified 

where one control device could achieve reductions in multiple 

pollutants, for example a fabric filter was expected to achieve 

both PM and mercury control in order to avoid overestimating the 

costs. We also included costs for testing and monitoring 

requirements contained in the proposed rule. The resulting total 

national cost impact of the proposed rule is 10.0 billion 
148

dollars in capital expenditures and 3.5 billion dollars per year 

in total annual costs. Considering estimated fuel savings 

resulting from work practice standards and combustion controls, 

the total annualized costs are reduced to 3.1 billion. The 

total capital and annual costs include costs for control 

devices, work practices, testing and monitoring. Table 11 of 

this preamble shows the capital and annual cost impacts for each 

subcategory. Costs include testing and monitoring costs, but 

not recordkeeping and reporting costs.

TABLE 11. SUMMARY OF CAPITAL AND ANNUAL COSTS FOR NEW AND 

EXISTING SOURCES

Source Subcategory Estimated/

Projected 

No. of 

Affected 

Units

Capital 

Costs 

(106$)

Testing 

and 

Monitoring 

Annualized 

Costs

(106$/yr)

Annualized 

Cost 

(106$/yr)

Existing 

Units

Coal units 578 4,880 62.6 1,854

Biomass 

units

420 2,003 37.1 613

Liquid 

units

826 1,487 30.7 503

Gas (NG/RG) 

units

11,532 75 0 33

Gas (other) 

units

199 1,554 10.2 481

Energy 

Audit

ALL 26

New Units Coal units 0 0 0 0

Biomass 0 0 0 0
149

units

Liquid 

units

11 12 0.5 6.1

Gas (NG/RG) 

units

33 0.2 0 0.01

Gas (other) 

units

2 5.5 0.14 1.7

Using Department of Energy projections on fuel 

expenditures, the number of additional boilers that could be 

potentially constructed was estimated. The resulting total 

national cost impact of the proposed rule in the 3rd year is 17

million dollars in capital expenditures and 6.2 million dollars 

per year in total annual costs, when considering a 1 percent 

fuel savings. 

Potential control device cost savings and increased 

recordkeeping and reporting costs associated with the emissions 

averaging provisions in the proposed rule are not accounted for

in either the capital or annualized cost estimates.

A discussion of the methodology used to estimate cost 

impacts is presented in “Methodology and Results of Estimating 

the Cost of Complying with the Industrial, Commercial, and 

Institutional Boiler and Process Heater NESHAP (2010)” in the 

Docket.

E. What are the economic impacts?
150

The economic impact analysis (EIA) that is included in the

RIA shows that the expected prices for industrial sectors could 

be 0.01 percent higher and domestic production may fall by about 

0.01 percent. Because of higher domestic prices imports may 

rise by 0.01 percent. In addition, impacts to affected energy 

markets show that prices may rise by 0.2 percent. 

 Social costs are estimated to also be $5.1 billion in 2008 

dollars. This is estimated to be made up of a $1.8 billion loss 

in domestic consumer surplus, a $3.8 billion loss in domestic 

producer surplus, a $0.2 billion increase in rest of the world 

surplus, and a $0.43 billion in net fuel savings not modeled in 

a way that can be used to attribute it to consumers and 

producers.

 EPA performed a screening analysis for impacts on small 

entities by comparing compliance costs to sales/revenues (e.g., 

sales and revenue tests). EPA’s analysis found the tests were 

typically higher than 3% for small entities included in the 

screening analysis. EPA has prepared an Initial Regulatory 

Flexibility Analysis (IRFA) that discusses alternative 

regulatory or policy options that minimize the rule’s small 

entity impacts. It includes key information about key results 

from the Small Business Advocacy Review (SBAR) panel.
151

 Estimates of job changes were developed in two different 

ways. The first is based on assuming job changes proportional 

to output changes. This approach provides a point estimate of 

8,000 less jobs; data is not available to estimate uncertainty 

ranges. This does not include job increases associated with 

pollutant abatement activities that require additional labor to 

produce the same level of output or changes related to post 

regulation production technologies. The second approach is more 

comprehensive and looks more directly at all three components 

but is based on a limited set of industrial data. This second 

method showed a point estimate of a net increase of about 8,000 

in jobs. However, statistical analysis of the data indicates 

that we can not state whether the net change will be an increase 

or a decrease using the second method.

F. 

We estimate the monetized benefits of this proposed 

regulatory action to be $16 billion to $40 billion (2008$, 3 

percent discount rate) in the implementation year (2013). The 

monetized benefits of the proposed regulatory action at a 7 

percent discount rate are $15 billion to $36 billion (2008$). 

Using alternate relationships between PM2.5 and premature 

mortality supplied by experts, higher and lower benefits 

estimates are plausible, but most of the expert-based estimates 

What are the social costs and benefits of this proposed rule?
152

fall between these two estimates.9

TABLE 12. Summary of the Monetized Benefits Estimates for the 

Proposed Boiler MACT for Major Sources in 2013 (billions of 

2008$)1

 A summary of the monetized 

benefits estimates at discount rates of 3 percent and 7 percent 

is in Table 12 of this preamble. 

Estimated Emission 

reductions

(tons per year)

Total monetized 

benefits

(3% Discount Rate)

Total monetized 

benefits

(7% Discount Rate)

22,662 tons PM2.5

384,024 tons SO2

1,436 tons VOC

$16 to $40 $15 to $36

1

All estimates are for the implementation year (2013), and are 

rounded to two significant figures so numbers may not sum across 

rows. All fine particles are assumed to have equivalent health 

effects, but the benefit-per-ton estimates vary between 

precursors because each ton of precursor reduced has a different 

propensity to form PM2.5. Benefits from reducing hazardous air 

pollutants (HAPs) are not included. 

These benefits estimates represent the total monetized 

human health benefits for populations exposed to less PM2.5 in 

2013 from controls installed to reduce air pollutants in order 

to meet these standards. These estimates are calculated as the 

sum of the monetized value of avoided premature mortality and 

morbidity associated with reducing a ton of PM2.5 and PM2.5

precursor emissions. To estimate of human health benefits 

derived from reducing PM2.5 and PM2.5 precursor emissions, we 

 

9 Roman et al, 2008. Expert Judgment Assessment of the Mortality 

Impact of Changes in Ambient Fine Particulate Matter in the U.S. 

Environ. Sci. Technol., 42, 7, 2268 – 2274.
153

utilized the general approach and methodology on the laid out in 

Fann et al. (2009)10

To generate the benefit-per-ton estimates, we used a model 

to convert emissions of direct PM2.5 and PM2.5 precursors into 

changes in ambient PM2.5 levels and another model to estimate the 

changes in human health associated with that change in air 

quality. Finally, the monetized health benefits were divided by 

the emission reductions to create the benefit-per-ton estimates. 

Even though we assume that all fine particles have equivalent 

health effects, the benefit-per-ton estimates vary between 

precursors because each ton of precursor reduced has a different 

propensity to form PM2.5. For example, SOX has a lower benefitper-ton estimate than direct PM2.5 because it does not form as 

much PM2.5, thus the exposure would be lower, and the monetized 

health benefits would be lower. 

. 

For context, it is important to note that the magnitude of 

the PM benefits is largely driven by the concentration response 

function for premature mortality. Experts have advised EPA to 

consider a variety of assumptions, including estimates based 

both on empirical (epidemiological) studies and judgments 

elicited from scientific experts, to characterize the 

 

10 Fann, N., C.M. Fulcher, B.J. Hubbell. 2009. The influence of location, 

source, and emission type in estimates of the human health benefits of 

reducing a ton of air pollution. Air Qual Atmos Health (2009) 2:169–176.
154

uncertainty in the relationship between PM2.5 concentrations and 

premature mortality. For this proposed rule we cite two key 

empirical studies, one based on the American Cancer Society 

cohort study11 and the extended Six Cities cohort study12

This analysis does not include the type of detailed 

uncertainty assessment found in the 2006 PM2.5 NAAQS RIA because 

we lack the necessary air quality input and monitoring data to 

run the benefits model. However, the 2006 PM2.5 NAAQS benefits 

analysis

. In 

the RIA for this proposed rule, which is available in the 

docket, we also include benefits estimates derived from expert 

judgments and other assumptions.

13

It should be emphasized that the monetized benefits 

estimates provided above do not include benefits from several 

important benefit categories, including reducing other air 

pollutants, ecosystem effects, and visibility impairment. The 

benefits from reducing carbon monoxide and hazardous air 

provides an indication of the sensitivity of our 

results to various assumptions. 

 

11 Pope et al, 2002. “Lung Cancer, Cardiopulmonary Mortality, 

and Long-term Exposure to Fine Particulate Air Pollution.” 

Journal of the American Medical Association 287:1132-1141

12 Laden et al, 2006. “Reduction in Fine Particulate Air 

Pollution and Mortality.” American Journal of Respiratory and 

Critical Care Medicine. 173: 667-672 13 U.S. Environmental Protection Agency, 2006. Final Regulatory Impact 

Analysis: PM2.5 NAAQS. Prepared by Office of Air and Radiation. October. 

Available on the Internet at http://www.epa.gov/ttn/ecas/ria.html
155

pollutants have not been monetized in this analysis, including 

reducing 360,000 tons of carbon monoxide, 19 tons of mercury, 

47,000 tons of HCl, and 1,200 tons of HF each year. Although we 

do not have sufficient information or modeling available to 

provide monetized estimates for this rulemaking, we include a 

qualitative assessment of the health effects of these air 

pollutants in the Regulatory Impact Analysis (RIA) for this 

proposed rule, which is available in the docket.

The social costs of this proposed rulemaking are estimated 

to be $5.1 billion (2008$) in the implementation year, and the 

monetized benefits are $16 billion to $40 billion (2008$, 3 

percent discount rate) for that same year. The benefits at a 7 

percent discount rate are $15 billion to $36 billion (2008$). 

Thus, net benefits of this rulemaking are estimated at $11 

billion to $35 billion (2008$, 3 percent discount rate) and $9.8 

billion to $31 billion (2008$, 7 percent discount rate). EPA 

believes that the benefits of the proposed rule are likely to 

exceed the costs even when taking into account the uncertainties 

in the cost and benefit estimates. 

For more information on the benefits analysis, please refer 

to the RIA for this rulemaking, which is available in the 

docket.

VI. Public Participation and Requests for Comment
156

We request comment on all aspects of this proposed rule. 

In 2004 we published a final rule for boilers and process 

heaters located at major source facilities (69 FR 55218, 

September 13, 2004). The final rule was vacated by the Court on 

June 19, 2007. We are reissuing our proposal, in response to 

the Court’s decisions, in this notice. We received many 

comments on that vacated rule during its rulemaking and have 

attempted to take all those comments into account in this 

action. This proposal includes a variety of changes from the 

vacated rule, mostly centered on emission limits for the various 

HAP and subcategories.

During this rulemaking, we conducted outreach to small 

entities and convened a Small Business Advocacy Review (SBAR)

Panel to obtain advice and recommendation of representatives of 

the small entities that potentially would be subject to the

requirements of this proposed rule. As part of the SBAR Panel 

process we conducted outreach with representatives from various 

small entities that would be affected by this proposed rule. We 

met with these small entity representatives (SERs) to discuss 

the potential rulemaking approaches and potential options to

decrease the impact of the rulemaking on their 

industries/sectors. We distributed outreach materials to the 

SERs; these materials included background on the rulemaking, 
157

possible regulatory approaches, preliminary cost and economic 

impacts, and possible rulemaking alternatives. We met with SERs 

from the industries that will be impacted directly by this 

proposed rule to discuss the outreach materials and receive 

feedback on the approaches and alternatives detailed in the 

outreach packet. The Panel received written comments from the

SERs following the meeting in response to discussions at the 

meeting and the questions posed to the SERs by the Agency. The 

SERs were specifically asked to provide comment on regulatory

alternatives that could help to minimize the rule’s impact on 

small businesses.

VII. Relationship of this Proposed Action to Section 112(c)(6) 

of the CAA

Section 112(c)(6) of the CAA requires EPA to identify 

categories of sources of seven specified pollutants to assure 

that sources accounting for not less than 90 percent of the 

aggregate emissions of each such pollutant are subject to

standards under CAA Section 112(d)(2) or 112(d)(4). EPA has 

identified “Industrial Coal Combustion,” “Industrial Oil 

Combustion,” Industrial Wood/Wood Residue Combustion,” 

“Commercial Coal Combustion,” “Commercial Oil Combustion,” and 

“Commercial Wood/Wood Residue Combustion” as source categories

that emits two of the seven CAA Section 112(c)(6) pollutants: 
158

POM and mercury. (The POM emitted is composed of 16 

polyaromatic hydrocarbons and extractable

organic matter.) In the Federal Register notice Source Category 

Listing for Section 112(d)(2) Rulemaking

Pursuant to Section 112(c)(6) Requirements, 63 FR 17838, 17849,

Table 2 (1998), EPA identified “Industrial Coal Combustion,” 

“Industrial Oil Combustion,” “Industrial Wood/Wood Residue 

Combustion,” “Commercial Coal Combustion,” “Commercial Oil 

Combustion,” and “Commercial Wood/Wood Residue Combustion” as 

source category “subject to regulation” for purposes of CAA 

Section 112(c)(6) with respect to the CAA Section 112(c)(6) 

pollutants that these units emit.

Specifically, as byproducts of combustion, the formation of 

POM is effectively reduced by the combustion and post-combustion

practices required to comply with the CAA Section 112 standards. 

Any POM that do form during combustion are further controlled by 

the various post-combustion controls. The add-on PM control

systems (either fabric filter or wet scrubber) and activated 

carbon injection in the fabric filter-based systems further

reduce emissions of these organic pollutants, and also reduce 

mercury emissions, as is evidenced by performance data. 

Specifically, the emission tests obtained at currently
159

operating units show that the proposed MACT regulations will

reduce mercury emissions by about 86 percent. It is, therefore, 

reasonable to conclude that POM emissions will be substantially 

controlled. Thus, while this proposed rule does not identify 

specific numerical emission limits for POM, emissions of POM

are, for the reasons noted below, nonetheless “subject to 

regulation” for purposes of Section 112(c)(6) of the CAA.

In lieu of establishing numerical emissions limits for 

pollutants such as POM, CAA Section 129(a)(4) allows EPA to 

regulate surrogate substances. While we have not identified 

specific numerical limits for POM, we believe CO serves as an 

effective surrogate for this HAP, because CO, like POM, is 

formed as a byproduct of combustion. 

Consequently, we have concluded that the emissions limits 

for CO function as a surrogate for control of POM, such that it 

is not necessary to propose numerical emissions limits for POM 

with respect to boilers and process heaters to satisfy CAA 

Section 112(c)(6).

To further address POM and mercury emissions, this proposed

rule also includes an energy assessment provision that encourage 

modifications to the facility to reduce energy demand that lead 

to these emissions.

VIII. Statutory and Executive Order Reviews
160

A. Executive Order 12866, Regulatory Planning and Review

Under Executive Order 12866 (58 FR 51735, October 4, 1993), 

this action is an “economically significant regulatory action” 

because it is likely to have an annual effect on the economy of 

$100 million or more or adversely affect in a material way the 

economy, a sector of the economy, productivity, competition, 

jobs, the environment, public health or safety, or State, local, 

or tribal governments or communities.

Accordingly, EPA submitted this action to the Office of 

Management and Budget (OMB) for review under EO 12866 and any 

changes in response to OMB recommendations have been documented 

in the docket for this action.

B. Executive Order 13132, Federalism

Executive Order 13132 (64 FR 43255, August 10, 1999), 

requires EPA to develop an accountable process to ensure 

“meaningful and timely input by State and local officials in the 

development of regulatory policies that have federalism 

implications.” “Policies that have federalism implications” is 

defined in the Executive Order to include regulations that have 

“substantial direct effects on the States, on the relationship 

between the national government and the States, or on the 

distribution of power and responsibilities among the various 

levels of government.
161

This proposed rule does not have federalism implications. 

It will not have substantial direct effects on the States, on 

the relationship between the national government and the States, 

or on the distribution of power and responsibilities among the 

various levels of government, as specified in Executive Order 

13132. Thus, Executive Order 13132 does not apply to this

proposed rule. In the spirit of Executive Order 13132, and 

consistent with EPA policy to promote communications between EPA 

and State and local governments, EPA specifically solicited 

comment on this proposed rule from State and local officials.

C. Executive Order 13175, Consultation and Coordination with 

Indian Tribal Governments

Executive Order 13175 (65 FR 67249, November 9, 2000), 

requires EPA to develop an accountable process to ensure 

“meaningful and timely input by tribal officials in the 

development of regulatory policies that have tribal 

implications.” This proposed rule does not have tribal 

implications, as specified in Executive Order 13175 (65 FR 

67249, November 9, 2000). It will not have substantial direct 

effects on tribal governments, on the relationship between the 

Federal government and Indian tribes, or on the distribution of 

power and responsibilities between the Federal government and 

Indian tribes, as specified in Executive Order 13175. This
162

proposed rule imposes requirements on owners and operators of 

specified area sources and not tribal governments. We do not 

know of any industrial, commercial, or institutional boilers 

owned or operated by Indian tribal governments. However, if 

there are any, the effect of this proposed rule on communities 

of tribal governments would not be unique or disproportionate to 

the effect on other communities. Thus, Executive Order 13175 

does not apply to this proposed rule. EPA specifically solicits 

additional comment on this proposed rule from tribal officials.

D. Executive Order 13045, Protection of Children from 

Environmental Health Risks and Safety Risks

Executive Order 13045 (62 FR 19885, April 23, 1997) applies 

to any rule that: (1) is determined to be “economically 

significant” as defined under Executive Order 12866, and (2) 

concerns an environmental health or safety risk that EPA has 

reason to believe may have a disproportionate effect on 

children. If the regulatory action meets both criteria, the 

Agency must evaluate the environmental health or safety effects 

of this planned rule on children, and explain why this planned 

regulation is preferable to other potentially effective and 

reasonably feasible alternatives considered by the Agency.

This proposed rule is not subject to Executive Order 13045 

because the Agency does not believe the environmental health 
163

risks or safety risks addressed by this action present a 

disproportionate risk to children. The reason for this 

determination is that this proposed rule is based solely on 

technology performance.

The public is invited to submit comments or identify peerreviewed studies and data that assess effects of early life 

exposure to this proposed rule. 

E. Unfunded Mandates Reform Act of 1995

Title II of the Unfunded Mandates Reform Act of 1995 

(UMRA), Public Law 104-4, establishes requirements for Federal 

agencies to assess the effects of their regulatory actions on 

State, local, and tribal governments and the private sector. 

Under section 202 of the UMRA, we generally must prepare a 

written statement, including a cost-benefit analysis, for 

proposed and final rules with “Federal mandates” that may result 

in expenditures to State, local, and tribal governments, in the 

aggregate, or to the private sector, of $100 million or more in 

any 1 year. Before promulgating a rule for which a written 

statement is needed, section 205 of the UMRA generally requires 

us to identify and consider a reasonable number of regulatory 

alternatives and adopt the least costly, most cost-effective or 

least burdensome alternative that achieves the objectives of the 

rule. The provisions of section 205 do not apply when they are 
164

inconsistent with applicable law. Moreover, section 205 allows 

us to adopt an alternative other than the least costly, most 

cost-effective or least burdensome alternative if the 

Administrator publishes with the final rule an explanation why 

that alternative was not adopted. Before we establish any 

regulatory requirements that may significantly or uniquely 

affect small governments, including tribal governments, we must 

develop a small government agency plan under section 203 of the 

UMRA. The plan must provide for notifying potentially affected 

small governments, enabling officials of affected small 

governments to have meaningful and timely input in the 

development of regulatory proposals with significant Federal 

intergovernmental mandates, and informing, educating, and 

advising small governments on compliance with the regulatory 

requirements.

We have determined that this proposed rule contains a 

Federal mandate that may result in expenditures of $100 million 

or more for State, local, and Tribal governments, in the 

aggregate, or the private sector in any 1 year. Accordingly, we 

have prepared a written statement entitled “Unfunded Mandates 

Reform Act Analysis for the Proposed Industrial Boilers and 

Process Heaters NESHAP" under section 202 of the UMRA which is 

summarized below.
165

1. Statutory Authority

As discussed in section I of this preamble, the statutory 

authority for this proposed rulemaking is section 112 of the 

CAA. Title III of the CAA Amendments was enacted to reduce 

nationwide air toxic emissions. Section 112(b) of the CAA lists 

the 188 chemicals, compounds, or groups of chemicals deemed by 

Congress to be HAP. These toxic air pollutants are to be 

regulated by NESHAP.

Section 112(d) of the CAA directs us to develop NESHAP 

which require existing and new major sources to control 

emissions of HAP using MACT based standards. This NESHAP 

applies to all industrial, commercial, and institutional boilers 

and process heaters located at major sources of HAP emissions.

In compliance with section 205(a) of the UMRA, we 

identified and considered a reasonable number of regulatory 

alternatives. Additional information on the costs and 

environmental impacts of these regulatory alternatives is 

presented in the docket.

The regulatory alternative upon which the proposed rule is 

based represents the MACT floor for industrial boilers and 

process heaters and, as a result, it is the least costly and 

least burdensome alternative.

2. Social Costs and Benefits
166

The regulatory impact analysis prepared for the proposed 

rule including the Agency’s assessment of costs and benefits, is 

detailed in the “Regulatory Impact Analysis for the Proposed 

Industrial Boilers and Process Heaters MACT” in the docket. 

Based on estimated compliance costs associated with the proposed 

rule and the predicted change in prices and production in the 

affected industries, the estimated social costs of the proposed 

rule are $5.1 billion (2008 dollars).

 It is estimated that 3 years after implementation of the 

proposed rule, HAPs would be reduced by thousands of tons, 

including reductions in hydrochloric acid, hydrogen fluoride, 

metallic HAP including mercury, and several other organic HAP 

from boilers and process heaters. Studies have determined a 

relationship between exposure to these HAP and the onset of 

cancer, however, the Agency is unable to provide a monetized 

estimate of the HAP benefits at this time. In addition, there 

are significant reductions in PM2.5 and in SO2 that would occur, 

including 23 thousand tons of PM2.5 and 384 thousand tons of SO2. 

These reductions occur within 3 years after the implementation 

of the proposed regulation and are expected to continue 

throughout the life of the affected sources. The major health 

effect associated with reducing PM2.5 and PM2.5 precursors (such 

as SO2) is a reduction in premature mortality. Other health 
167

effects associated with PM2.5 emission reductions include 

avoiding cases of chronic bronchitis, heart attacks, asthma 

attacks, and work-lost days (i.e., days when employees are 

unable to work). While we are unable to monetize the benefits 

associated with the HAP emissions reductions, we are able to 

monetize the benefits associated with the PM2.5 and SO2 emissions 

reductions. For SO2 and PM2.5, we estimated the benefits 

associated with health effects of PM but were unable to quantify 

all categories of benefits (particularly those associated with 

ecosystem and visibility effects). Our estimates of the 

monetized benefits in 2013 associated with the implementation of 

the proposed alternative is range from $16 billion (2008 

dollars)to $40 billion (2008 dollars) when using a 3 percent 

discount rate (or from $15 billion (2008 dollars)to $36 billion 

(2008 dollars) when using a 7 percent discount rate). This 

estimate, at a 3 percent discount rate, is about $11 billion 

(2008 dollars) to $35 billion (2008 dollars) higher than the 

estimated social costs shown earlier in this section. The 

general approach used to value benefits is discussed in more 

detail earlier in this preamble. For more detailed information 

on the benefits estimated for the proposed rulemaking, refer to 

the RIA in the docket.

3. Future and Disproportionate Costs
168

The Unfunded Mandates Act requires that we estimate, where 

accurate estimation is reasonably feasible, future compliance 

costs imposed by the proposed rule and any disproportionate 

budgetary effects. Our estimates of the future compliance costs 

of the proposed rule are discussed previously in this preamble.

We do not believe that there will be any disproportionate 

budgetary effects of the proposed rule on any particular areas 

of the country, State or local governments, types of communities 

(e.g., urban, rural), or particular industry segments. See the 

results of the “Economic Impact Analysis of the Proposed 

Industrial Boilers and Process Heaters NESHAP,” the results of 

which are discussed previously in this preamble.

4. Effects on the National Economy

The Unfunded Mandates Act requires that we estimate the 

effect of the proposed rule on the national economy. To the 

extent feasible, we must estimate the effect on productivity, 

economic growth, full employment, creation of productive jobs, 

and international competitiveness of the U.S. goods and 

services, if we determine that accurate estimates are reasonably 

feasible and that such effect is relevant and material.

The nationwide economic impact of the proposed rule is 

presented in the “Economic Impact Analysis for the Industrial 

Boilers and Process Heaters MACT” in the docket. This analysis 
169

provides estimates of the effect of the proposed rule on some of 

the categories mentioned above. The results of the economic 

impact analysis are summarized previously in this preamble. The 

results show that there will be a small impact on prices and 

output, and little impact on communities that may be affected by 

the proposed rule. In addition, there should be little impact 

on energy markets (in this case, coal, natural gas, petroleum 

products, and electricity). Hence, the potential impacts on the 

categories mentioned above should be small.

5. Consultation with Government Officials

The Unfunded Mandates Act requires that we describe the 

extent of the Agency’s prior consultation with affected State, 

local, and tribal officials, summarize the officials’ comments 

or concerns, and summarize our response to those comments or 

concerns. In addition, section 203 of the UMRA requires that we 

develop a plan for informing and advising small governments that 

may be significantly or uniquely impacted by a proposal. 

Although the proposed rule does not affect any State, local, or 

Tribal governments, we have consulted with State and local air 

pollution control officials. We also have held meetings on the 

proposed rule with many of the stakeholders from numerous 

individual companies, environmental groups, consultants and 
170

vendors, labor unions, and other interested parties. We have 

added materials to the Air Docket to document these meetings.

In addition, we have determined that the proposed rule 

contains no regulatory requirements that might significantly or 

uniquely affect small governments. While some small governments 

may have some sources affected by the proposed rule, the impacts 

are not expected to be significant. Therefore, today's proposed 

rule is not subject to the requirements of section 203 of the 

UMRA.

F. Regulatory Flexibility Act (RFA), as Amended by the Small 

Business Regulatory Enforcement Fairness Act of 1996 (SBREFA), 5 

U.S.C. 601 et seq.

The RFA generally requires an agency to prepare a 

regulatory flexibility analysis of any rule subject to notice 

and comment rulemaking requirements under the Administrative 

Procedure Act or any other statute unless the agency certifies 

that the rule will not have a significant economic impact on a 

substantial number of small entities. Small entities include 

small businesses, small organizations, and small governmental 

jurisdictions.

For purposes of assessing the impacts of today’s proposed 

rule on small entities, small entity is defined as: (1) a small 

business according to Small Business Administration (SBA) size 
171

standards by the North American Industry Classification System 

category of the owning entity. The range of small business size 

standards for the 40 affected industries ranges from 500 to 

1,000 employees, except for petroleum refining and electric 

utilities. In these latter two industries, the size standard is 

1,500 employees and a mass throughput of 75,000 barrels/day or 

less, and 4 million kilowatt-hours of production or less, 

respectively; (2) a small governmental jurisdiction that is a 

government of a city, county, town, school district or special 

district with a population of less than 50,000; and (3) a small 

organization that is any not-for-profit enterprise which is 

independently owned and operated and is not dominant in its 

field. 

Because an initial screening analysis for impact on small 

entities indicated a likely significant impact for substantial

numbers EPA convened a SBAR Panel to obtain advice and 

recommendation of representatives of the small entities that

potentially would be subject to the requirements of this rule.

(a) Panel Process and Panel Outreach

As required by section 609(b) of the RFA, as amended by 

SBREFA, EPA also has conducted outreach to small entities and. 

On January 22, 2009 EPA’s Small Business Advocacy Chairperson 

convened a Panel under section 609(b) of the RFA. In addition 
172

to the Chair, the Panel consisted of the Director of the Sector 

Policies and Programs Division within EPA’s Office of Air and 

Radiation, the Chief Counsel for Advocacy of the Small Business

Administration, and the Administrator of the Office of 

Information and Regulatory Affairs within the Office of

Management and Budget.

As part of the SBAR Panel process we conducted outreach 

with representatives from 14 various small entities that would 

be affected by this rule. The small entity representatives 

(SERs) included associations representing schools, churches, 

hotels/motels, wood product facilities and manufacturers of home 

furnishings. We met with these SERs to discuss the potential 

rulemaking approaches and potential options to decrease the 

impact of the rulemaking on their industries/sectors. We 

distributed outreach materials to the SERs; these materials 

included background on the rulemaking, possible regulatory

approaches, preliminary cost and economic impacts, and possible 

rulemaking alternatives. The Panel met with SERs from the 

industries that will be impacted directly by this rule on

February 10, 2009 to discuss the outreach materials and receive 

feedback on the approaches and alternatives detailed in the 

outreach packet. (EPA also met with SERs on November 13, 2008

for an initial outreach meeting.) The Panel received written 
173

comments from the SERs following the meeting in response to 

discussions at the meeting and the questions posed to the SERs 

by the Agency. The SERs were specifically asked to provide 

comment on regulatory alternatives that could help to minimize

the rule’s impact on small businesses.

(1) Panel Recommendations for Small Business Flexibilities

The Panel recommended that EPA consider and seek comment on 

a wide range of regulatory alternatives to mitigate the impacts 

of the rulemaking on small businesses, including those

flexibility options described below. The following section 

summarizes the SBAR Panel recommendations. EPA has proposed 

provisions consistent with four of the Panel’s recommendations.

Consistent with the RFA/SBREFA requirements, the Panel 

evaluated the assembled materials and small-entity comments on 

issues related to elements of the IRFA. A copy of the Final 

Panel Report (including all comments received from SERs in 

response to the Panel’s outreach meeting as well as summaries of 

both outreach meetings that were held with the SERs is included 

in the docket for this proposed rule. A summary of the Panel 

recommendations is detailed below. As noted above, this 

proposal includes proposed provisions for all but one of the 

Panel recommendations.

(a) Work Practice Standards
174

The panel recommended that EPA consider requiring annual 

tune-ups, including standardized criteria outlining proper tuneup methods targeted at smaller boiler operators. The panel 

further recommended that EPA take comment on the efficacy of 

energy assessments/audits at improving combustion efficiency and 

the cost of performing the audits, especially to smaller boiler 

operators.

A work practice standard, instead of MACT emission limits, 

may be proposed if it can be justified under section 112(h) of 

the CAA, that is, it is impracticable to enforce the emission 

standards due to technical or economic limitations. Work 

practice standards could reduce fuel use and improve combustion 

efficiency which would result in reduced emissions.

In general, SERs commented that a regulatory approach to 

improve combustion efficiency, such as work practice standards, 

would have positive impacts with respect to the environment and 

energy use and save on compliance costs. The SERs were 

concerned with work practice standards that would require energy 

audits and implementation of audit findings. The basis of these 

concerns rested upon the uncertainty that there is no guarantee 

that there are available funds to implement a particular audit’s 

findings.

(b) Subcategorization
175

The Panel recommended that EPA allow subcategorizations 

suggested by the SERs, unless EPA finds that a subcategorization 

is inconsistent with the Clean Air Act. 

SERs commented that subcategorization is a key concept that 

could ensure that like boilers are compared with similar boilers 

so that MACT floors are more reasonable and could be achieved by 

all units within a subcategory using appropriate emission 

reduction strategies. SERs commented that EPA should 

subcategorize based on fuel type, boiler type, duty cycle, and 

location. 

(c) Health Based Compliance Alternatives (HBCA)

The Panel recommended that EPA adopt the HBCA as a 

regulatory flexibility option for the Boiler MACT rulemaking. 

The panel recognized, however, that EPA has concerns about its 

legal authority to provide an HBCA under the Clean Air Act, and 

EPA may ultimately determine that this flexibility is 

inconsistent with the Clean Air Act.

SERs commented that adopting an HBCA would perhaps be the 

most important step EPA could take to mitigate the serious 

financial harm the Boiler MACT would otherwise inflict on small 

entities using solid fuels nationwide and, therefore, HBCA 

should be a critical component of any future rule to lessen 

impact on small entities.
176

(d) Emissions Averaging

The Panel recommended that EPA consider a provision for 

emission averaging and long averaging times for the proposed 

emission limits.

SERs commented that a measure EPA should consider to lessen 

the regulatory burden of complying with Boiler MACT is to allow 

emissions averaging at sources with multiple regulated units. 

SERs commented that another approach that can aide small entity 

compliance is to set longer averaging times (i.e., 30-days or 

more) rather than looking at a mere 3-run (hour) average for 

performance. Given the inherent variability in boiler 

performance, an annual or quarterly averaging period for all HAP 

would prevent a single spike in emissions from throwing a unit 

into non-compliance.

(e) Compliance Costs

The Panel recommended that EPA carefully weigh the 

potential burden of compliance requirements and consider for 

small entities options such as, emission averaging within 

facility, reduced monitoring/testing requirements, or allowing 

more time for compliance. 

SERs noted that recordkeeping activities, as written in the 

vacated boiler MACT, would be especially challenging for small 
177

entities that do not have a dedicated environmental affairs 

department. 

G. Paperwork Reduction Act

The information collection requirements in the proposed 

rule will be submitted for approval to the Office of Management 

and Budget under the Paperwork Reduction Act, 44 U.S.C. 3501 et

seq. An Information Collection Request (ICR) document has been 

prepared by EPA (ICR No. 2028.01).

 The information requirements are based on notification, 

recordkeeping, and reporting requirements in the NESHAP General 

Provisions (40 CFR part 63, subpart A), which are mandatory for 

all operators subject to national emission standards. These 

recordkeeping and reporting requirements are specifically 

authorized by section 114 of the CAA (42 U.S.C. 7414). All 

information submitted to EPA pursuant to the recordkeeping and 

reporting requirements for which a claim of confidentiality is 

made is safeguarded according to Agency policies set forth in 40 

CFR part 2, subpart B.

The proposed rule would require maintenance inspections of 

the control devices but would not require any notifications or 

reports beyond those required by the General Provisions. The 

recordkeeping requirements require only the specific information 

needed to determine compliance.
178

 The annual monitoring, reporting, and recordkeeping burden 

for this collection (averaged over the first 3 years after the 

effective date of the standards) is estimated to be $109 

million. This includes 364,942 labor hours per year at a total 

labor cost of $34.5 million per year, and total non-labor 

capital costs of $74.5 million per year. This estimate includes 

initial and annual performance test, conducting an documenting 

an energy audit, conducting and documenting a tune-up, 

semiannual excess emission reports, maintenance inspections, 

developing a monitoring plan, notifications, and recordkeeping. 

Monitoring, testing, tune-up and energy audit costs and cost 

were also included in the cost estimates presented in the 

control costs impacts estimates in section IV.D of this 

preamble. The total burden for the Federal government (averaged 

over the first 3 years after the effective date of the standard) 

is estimated to be 121,506 hours per year at a total labor cost 

of $6.4 million per year.

Burden means the total time, effort, or financial resources 

expended by persons to generate, maintain, retain, or disclose 

or provide information to or for a Federal agency. This 

includes the time needed to review instructions; develop, 

acquire, install, and utilize technology and systems for the 

purposes of collecting, validating, and verifying information, 
179

processing and maintaining information, and disclosing and 

providing information; adjust the existing ways to comply with 

any previously applicable instructions and requirements; train 

personnel to be able to respond to a collection of information; 

search data sources; complete and review the collection of 

information; and transmit or otherwise disclose the information.

 An Agency may not conduct or sponsor, and a person is not 

required to respond to, a collection of information unless it 

displays a currently valid OMB control number. The OMB control 

numbers for our regulations are listed in 40 CFR part 9 and 48 

CFR chapter 15.

To comment on EPA’s need for this information, the accuracy 

of the provided burden estimates, and any suggested methods for 

minimizing respondent burden, including the use of automated 

collection techniques, EPA has established a public docket for 

this action, which includes this ICR, under Docket ID number 

EPA-HQ-OAR-2002-0058. Submit any comments related to the ICR to 

EPA and OMB. See ADDRESSES section at the beginning of this 

preamble for where to submit comments to EPA. Send comments to 

OMB at the Office of Information and Regulatory Affairs, Office 

of Management and Budget, 725 17th Street, NW, Washington, DC 

20503, Attention: Desk Office for EPA. Since OMB is required 

to make a decision concerning the ICR between 30 and 60 days 
180

after [INSERT DATE OF PUBLICATION IN THE FEDERAL REGISTER], a 

comment to OMB is best assured of having its full effect if OMB 

receives it by [INSERT DATE 30 DAYS FROM DATE OF PUBLICATION IN 

THE FEDERAL REGISTER]. The final rule will respond to any OMB 

or public comments on the information collection requirements 

contained in this proposal.

H. National Technology Transfer and Advancement Act

Section 12(d) of the National Technology Transfer and 

Advancement Act (NTTAA) of 1995 (Public Law No. 104-113; 

15 U.S.C. 272 note) directs the EPA to use voluntary consensus 

standards in their regulatory and procurement activities unless 

to do so would be inconsistent with applicable law or otherwise 

impractical. Voluntary consensus standards are technical 

standards (e.g., materials specifications, test methods, 

sampling procedures, business practices) developed or adopted by 

one or more voluntary consensus bodies. The NTTAA directs EPA 

to provide Congress, through annual reports to the Office of 

Management and Budget, with explanations when an agency does not 

use available and applicable voluntary consensus standards. 

This rulemaking involves technical standards. The EPA 

cites the following standards in the proposed rule: EPA Methods 

1, 2, 2F, 2G, 3A, 3B, 4, 5, 5D, 17, 19, 26, 26A, 29 of 40 CFR 

part 60. Consistent with the NTTAA, EPA conducted searches to 
181

identify voluntary consensus standards in addition to these EPA 

methods. No applicable voluntary consensus standards were 

identified for EPA Methods 2F, 2G, 5D, and 19. The search and 

review results have been documented and are placed in the docket 

for the proposed rule. 

The three voluntary consensus standards described below 

were identified as acceptable alternatives to EPA test methods 

for the purposes of the proposed rule. 

The voluntary consensus standard ASME PTC 19-10-1981-Part 

10, “Flue and Exhaust Gas Analyses,” is cited in the proposed 

rule for its manual method for measuring the oxygen, carbon 

dioxide, and carbon monoxide content of exhaust gas. This part 

of ASME PTC 19-10-1981-Part 10 is an acceptable alternative to 

Method 3B.

The voluntary consensus standard ASTM D6522-00, “Standard 

Test Method for the Determination of Nitrogen Oxides, Carbon 

Monoxide, and Oxygen Concentrations in Emissions from Natural 

Gas-Fired Reciprocating Engines, Combustion Turbines, Boilers 

and Process Heaters Using Portable Analyzers” is an acceptable 

alternative to EPA Method 3A for identifying carbon monoxide and 

oxygen concentrations for the proposed rule when the fuel is 

natural gas. 
182

The voluntary consensus standard ASTM Z65907, “Standard 

Method for Both Speciated and Elemental Mercury Determination,” 

is an acceptable alternative to EPA Method 29 (portion for 

mercury only) for the purpose of the proposed rule. This 

standard can be used in the proposed rule to determine the 

mercury concentration in stack gases for boilers with rated heat 

input capacities of greater than 250 MMBtu per hour.

In addition to the voluntary consensus standards EPA uses 

in the proposed rule, the search for emissions measurement 

procedures identified 15 other voluntary consensus standards. 

The EPA determined that 13 of these 15 standards identified for 

measuring emissions of the HAP or surrogates subject to emission 

standards in the proposed rule were impractical alternatives to 

EPA test methods for the purposes of the rule. Therefore, EPA 

does not intend to adopt these standards for this purpose. The 

reasons for this determination for the 13 methods are discussed 

below.

The voluntary consensus standard ASTM D3154-00, “Standard 

Method for Average Velocity in a Duct (Pitot Tube Method),” is 

impractical as an alternative to EPA Methods 1, 2, 3B, and 4 for 

the purposes of the proposed rulemaking since the standard 

appears to lack in quality control and quality assurance 

requirements. Specifically, ASTM D3154-00 does not include the 
183

following: (1) proof that openings of standard pitot tube have 

not plugged during the test; (2) if differential pressure gauges 

other than inclined manometers (e.g., magnehelic gauges) are 

used, their calibration must be checked after each test series; 

and (3) the frequency and validity range for calibration of the 

temperature sensors.

The voluntary consensus standard ASTM D3464-96 (2001), 

“Standard Test Method Average Velocity in a Duct Using a Thermal 

Anemometer,” is impractical as an alternative to EPA Method 2 

for the purposes of the proposed rule primarily because 

applicability specifications are not clearly defined, e.g., 

range of gas composition, temperature limits. Also, the lack of 

supporting quality assurance data for the calibration procedures 

and specifications, and certain variability issues that are not 

adequately addressed by the standard limit EPA’s ability to make 

a definitive comparison of the method in these areas.

The voluntary consensus standard ISO 10780:1994, 

“Stationary Source Emissions–Measurement of Velocity and Volume 

Flowrate of Gas Streams in Ducts,” is impractical as an 

alternative to EPA Method 2 in the proposed rule. The standard 

recommends the use of an L-shaped pitot, which historically has 

not been recommended by EPA. The EPA specifies the S-type 
184

design which has large openings that are less likely to plug up 

with dust.

The voluntary consensus standard, CAN/CSA Z223.2-M86(1999), 

“Method for the Continuous Measurement of Oxygen, Carbon 

Dioxide, Carbon Monoxide, Sulphur Dioxide, and Oxides of 

Nitrogen in Enclosed Combustion Flue Gas Streams,” is 

unacceptable as a substitute for EPA Method 3A since it does not 

include quantitative specifications for measurement system 

performance, most notably the calibration procedures and 

instrument performance characteristics. The instrument 

performance characteristics that are provided are nonmandatory 

and also do not provide the same level of quality assurance as 

the EPA methods. For example, the zero and span/calibration 

drift is only checked weekly, whereas the EPA methods requires 

drift checks after each run.

Two very similar voluntary consensus standards, ASTM D5835-

95 (2001), “Standard Practice for Sampling Stationary Source 

Emissions for Automated Determination of Gas Concentration,” and 

ISO 10396:1993, “Stationary Source Emissions: Sampling for the 

Automated Determination of Gas Concentrations,” are impractical 

alternatives to EPA Method 3A for the purposes of the proposed 

rule because they lack in detail and quality assurance/quality 

control requirements. Specifically, these two standards do not 
185

include the following: (1) sensitivity of the method; 

(2) acceptable levels of analyzer calibration error; (3) 

acceptable levels of sampling system bias; (4) zero drift and 

calibration drift limits, time span, and required testing 

frequency; (5) a method to test the interference response of the 

analyzer; (6) procedures to determine the minimum sampling time 

per run and minimum measurement time; and (7) specifications for 

data recorders, in terms of resolution (all types) and recording 

intervals (digital and analog recorders, only).

The voluntary consensus standard ISO 12039:2001, 

“Stationary Source Emissions--Determination of Carbon Monoxide, 

Carbon Dioxide, and Oxygen--Automated Methods,” is not 

acceptable as an alternative to EPA Method 3A. This ISO 

standard is similar to EPA Method 3A, but is missing some key 

features. In terms of sampling, the hardware required by 

ISO 12039:2001 does not include a 3-way calibration valve 

assembly or equivalent to block the sample gas flow while 

calibration gases are introduced. In its calibration

procedures, ISO 12039:2001 only specifies a two-point 

calibration while EPA Method 3A specifies a three-point 

calibration. Also, ISO 12039:2001 does not specify performance 

criteria for calibration error, calibration drift, or sampling 
186

system bias tests as in the EPA method, although checks of these 

quality control features are required by the ISO standard. 

The voluntary consensus standard ASME PTC-38-80 R85 (1985), 

“Determination of the Concentration of Particulate Matter in Gas 

Streams,” is not acceptable as an alternative for EPA Method 5 

because ASTM PTC-38-80 is not specific about equipment 

requirements, and instead presents the options available and the 

pro’s and con’s of each option. The key specific differences 

between ASME PTC-38-80 and the EPA methods are that the ASME 

standard: (1) allows in-stack filter placement as compared to 

the out-of-stack filter placement in EPA Methods 5 and 17; 

(2) allows many different types of nozzles, pitots, and 

filtering equipment; (3) does not specify a filter weighing 

protocol or a minimum allowable filter weight fluctuation as in 

the EPA methods; and (4) allows filter paper to be only 

99 percent efficient, as compared to the 99.95 percent 

efficiency required by the EPA methods. 

The voluntary consensus standard ASTM D3685/D3685M-98, 

“Test Methods for Sampling and Determination of Particulate 

Matter in Stack Gases,” is similar to EPA Methods 5 and 17, but 

is lacking in the following areas that are needed to produce 

quality, representative particulate data: (1) requirement that 

the filter holder temperature should be between 120o

C and 134oC, 
187

and not just “above the acid dew-point;” (2) detailed 

specifications for measuring and monitoring the filter holder 

temperature during sampling; (3) procedures similar to EPA

Methods 1, 2, 3, and 4, that are required by EPA Method 5; (4) 

technical guidance for performing the Method 5 sampling 

procedures, e.g., maintaining and monitoring sampling train 

operating temperatures, specific leak check guidelines and 

procedures, and use of reagent blanks for determining and 

subtracting background contamination; and (5) detailed equipment 

and/or operational requirements, e.g., component exchange leak 

checks, use of glass cyclones for heavy particulate loading 

and/or water droplets, operating under a negative stack 

pressure, exchanging particulate loaded filters, sampling 

preparation and implementation guidance, sample recovery 

guidance, data reduction guidance, and particulate sample 

calculations input.

The voluntary consensus standard ISO 9096:1992, 

“Determination of Concentration and Mass Flow Rate of 

Particulate Matter in Gas Carrying Ducts - Manual Gravimetric 

Method,” is not acceptable as an alternative for EPA Method 5. 

Although sections of ISO 9096 incorporate EPA Methods 1, 2, and 

5 to some degree, this ISO standard is not equivalent to EPA 

Method 5 for collection of particulate matter. The standard ISO 
188

9096 does not provide applicable technical guidance for 

performing many of the integral procedures specified in Methods 

1, 2, and 5. Major performance and operational details are 

lacking or nonexistent, and detailed quality assurance/quality 

control guidance for the sampling operations required to produce 

quality, representative particulate data (e.g., guidance for 

maintaining and monitoring train operating temperatures, 

specific leak check guidelines and procedures, and sample 

preparation and recovery procedures) are not provided by the 

standard, as in EPA Method 5. Also, details of equipment and/or 

operational requirements, such as those specified in EPA 

Method 5, are not included in the ISO standard, e.g., stack gas 

moisture measurements, data reduction guidance, and particulate 

sample calculations. 

The voluntary consensus standard CAN/CSA Z223.1-M1977, 

“Method for the Determination of Particulate Mass Flows in 

Enclosed Gas Streams,” is not acceptable as an alternative for 

EPA Method 5. Detailed technical procedures and quality control 

measures that are required in EPA Methods 1, 2, 3, and 4 are not 

included in CAN/CSA Z223.1. Second, CAN/CSA Z223.1 does not 

include the EPA Method 5 filter weighing requirement to repeat 

weighing every 6 hours until a constant weight is achieved. 

Third, EPA Method 5 requires the filter weight to be reported to 
189

the nearest 0.1 mg, while CAN/CSA Z223.1 requires only to the 

nearest 0.5 mg. Also, CAN/CSA Z223.1 allows the use of a 

standard pitot for velocity measurement when plugging of the 

tube opening is not expected to be a problem. Whereas, EPA 

Method 5 requires an S-shaped pitot. 

The voluntary consensus standard EN 1911-1,2,3 (1998), 

“Stationary Source Emissions-Manual Method of Determination of 

HCl-Part 1: Sampling of Gases Ratified European Text-Part 2: 

Gaseous Compounds Absorption Ratified European Text-Part 3: 

Adsorption Solutions Analysis and Calculation Ratified European 

Text,” is impractical as an alternative to EPA Methods 26 and 

26A. Part 3 of this standard cannot be considered equivalent to 

EPA Method 26 or 26A because the sample absorbing solution 

(water) would be expected to capture both HCl and chlorine gas, 

if present, without the ability to distinguish between the two. 

The EPA Methods 26 and 26A use an acidified absorbing solution 

to first separate HCl and chlorine gas so that they can be 

selectively absorbed, analyzed, and reported separately. In 

addition, in EN 1911 the absorption efficiency for chlorine gas 

would be expected to vary as the pH of the water changed during 

sampling.

The voluntary consensus standard EN 13211 (1998), is not 

acceptable as an alternative to the mercury portion of EPA 
190

Method 29 primarily because it is not validated for use with 

impingers, as in the EPA method, although the method describes 

procedures for the use of impingers. This European standard is 

validated for the use of fritted bubblers only and requires the 

use of a side (split) stream arrangement for isokinetic sampling 

because of the low sampling rate of the bubblers (up to 3 liters 

per minute, maximum). Also, only two bubblers (or impingers) 

are required by EN 13211, whereas EPA Method 29 require the use 

of six impingers. In addition, EN 13211 does not include many 

of the quality control procedures of EPA Method 29, especially 

for the use and calibration of temperature sensors and 

controllers, sampling train assembly and disassembly, and filter 

weighing.

Two of the 15 voluntary consensus standards identified in 

this search were not available at the time the review was 

conducted for the purposes of the proposed rule because they are 

under development by a voluntary consensus body: ASME/BSR MFC 

13M, “Flow Measurement by Velocity Traverse,” for EPA Method 2 

(and possibly 1); and ASME/BSR MFC 12M, “Flow in Closed Conduits 

Using Multiport Averaging Pitot Primary Flowmeters,” for EPA 

Method 2. 

Section 63.7520 and Tables 4A through 4D to subpart DDDDD, 

40 CFR part 63, list the EPA testing methods included in the 
191

proposed rule. Under §63.7(f) and §63.8(f) of subpart A of the 

General Provisions, a source may apply to EPA for permission to 

use alternative test methods or alternative monitoring 

requirements in place of any of the EPA testing methods, 

performance specifications, or procedures.

I. Executive Order 13211, Actions Concerning Regulations That 

Significantly Affect Energy Supply, Distribution, or Use

Executive Order 13211, (66 FR 28355, May 22, 2001), 

provides that agencies shall prepare and submit to the 

Administrator of the Office of Information and Regulatory 

Affairs, Office of Management and Budget, a Statement of Energy 

Effects for certain actions identified as significant energy 

actions. Section 4(b) of Executive Order 13211 defines 

“significant energy actions” as “any action by an agency 

(normally published in the Federal Register) that promulgates or 

is expected to lead to the promulgation of a final rule or 

regulation, including notices of inquiry, advance notices of 

proposed rulemaking, and notices of proposed rulemaking: (1)(i) 

that is a significant regulatory action under Executive Order 

12866 or any successor order, and (ii) is likely to have a 

significant adverse effect on the supply, distribution, or use 

of energy; or (2) that is designated by the Administrator of the 

Office of Information and Regulatory Affairs as a significant 

energy action.” The proposed rule is not a “significant 
192

regulatory action” because it is not likely to have a 

significant adverse effect on the supply, distribution, or use 

of energy. The basis for the determination is as follows.

We estimate a 0.14% price increase for the energy sector 

and a 0.07% percentage change in production. We estimate a 

0.18% increase in energy imports. For more information on the 

estimated energy effects, please refer to the economic impact 

analysis for the proposed rule. The analysis is available in 

the public docket. 

Therefore, we conclude that the proposed rule when 

implemented is not likely to have a significant adverse effect 

on the supply, distribution, or use of energy. 

J. Executive Order 12898: Federal Actions to Address 

Environmental Justice in Minority Populations and Low-Income 

Populations

Executive Order 12898 (59 FR 7629, February 16, 1994) 

establishes Federal executive policy on environmental justice 

(EJ). Its main provision directs Federal agencies, to the 

greatest extent practicable and permitted by law, to make 

environmental justice part of their mission by identifying and 

addressing, as appropriate, disproportionately high and adverse 

human health or environmental effects of their programs, 

policies, and activities on minority populations, low-income, 

and Tribal populations in the United States.
193

This proposed action establishes national emission 

standards for new and existing industrial, commercial, 

institutional boilers and process heaters that combust non-waste 

materials (i.e. natural gas, process gas, fuel oil, biomass, and 

coal) and that are located at a major source. The EPA estimates 

that there are approximately 38,000 units covered by this rule.

The proposed rule will reduce emissions of all the listed 

HAP that come from boilers and process heaters. This includes 

metals (mercury, arsenic, beryllium, cadmium, chromium, lead, 

manganese, nickel, and selenium), organics (POM, acetaldehyde, 

acrolein, benzene, dioxins, ethylene dichloride, formaldehyde, 

and PCB), hydrochloric acid, hydrofluoric acid (See Table 6 of 

this preamble). Adverse health effects from these pollutants 

include cancer and chronic health disorders (e.g., irritation of 

the lung, skin, and mucus membranes, effects on the central 

nervous system, and damage to the kidneys), and acute health 

disorders (e.g., lung irritation and congestion, alimentary 

effects such as nausea and vomiting, and effects on the kidney 

and central nervous system). The rule will also result in 

substantial reductions of criteria pollutants (i.e. CO, PM, SO2) 

and ozone precursors.

EPA reviewed the distributions of baseline exposures to and 

risks from all HAP from all sources among different sociodemographic groups for this rule, and related the locations of 
194

expected emission reductions from this rule to the locations of 

higher than average cancer risks due to HAP, as estimated via 

EPA’s 2002 National Air Toxics Assessment (NATA). The review 

identified those census blocks within 3 miles of affected 

sources and determined the demographic composition (e.g. race, 

income, education, etc) of these census blocks. 

Based on the fact that the rule does not allow emission 

increases, the EPA has determined that the proposed rule will 

not have disproportionately high and adverse human health or 

environmental effects on minority, low-income, or Tribal 

populations. Also, based on the review of NATA results, 

estimated emission reductions associated with this rule, and the 

demographics within 3 miles of each boiler, EPA has determined 

that the greatest emission reductions tend to occur in the areas 

of higher total cancer risks from HAPs. These areas tend to 

have lower proportions of Whites and American Indians, higher 

proportions of African-Americans, Hispanics, and “Other and 

Multi-racial” populations, and higher proportions of families 

with incomes below the poverty level. However, to the extent 

that any minority, low income, or Tribal subpopulation is 

disproportionately impacted by the current emissions as a result 

of the proximity of their homes to these sources, that 

subpopulation also stands to see increased environmental and 
195

health benefit from the emissions reductions called for by this 

rule.

EPA defines “Environmental Justice” to include meaningful 

involvement of all people regardless of race, color, national 

origin, or income with respect to the development, 

implementation, and enforcement of environmental laws, 

regulations, and polices. To promote meaningful involvement, 

EPA has developed a communication and outreach strategy to 

ensure that interested communities have access to this proposed 

rule, are aware of its content, and have an opportunity to 

comment during the comment period. During the comment period, 

EPA will publicize the rulemaking via EJ newsletters, Tribal 

newsletters, EJ listserves, and the internet, including the 

Office of Policy, Economics, and Innovation’s (OPEI) Rulemaking 

Gateway web site 

(http://yosemite.epa.gov/opei/rulegate.nsf/content/index.html?op

endocument). EPA will also provide general rulemaking fact 

sheets (e.g., why is this important for my community) for EJ 

community groups and conduct conference calls and Webinars with 

interested communities. In addition, state and federal 

permitting requirements will provide state, local governments, 

and communities an opportunity to provide their comments on the 

permit conditions associated with permitting the sources 

affected by this rulemaking.
196
197

List of Subjects in 40 CFR part 63

Environmental protection, Administrative practice and 

procedure, Air pollution control, Hazardous substances, 

Intergovernmental relations, Reporting and recordkeeping 

requirements.

______________________

Dated:

_______________________

Lisa P. Jackson,

Administrator. 
198

For the reasons stated in the preamble, title 40, chapter 

I, part 63 of the Code of the Federal Regulations is 

proposed to be amended as follows:

PART 63--[AMENDED]

1. The authority citation for part 63 continues to read as 

follows:

Authority: 42 U.S.C. 7401, et seq.

2. Part 63 is amended by adding subpart DDDDD to read as 

follows:

Subpart DDDDD--National Emission Standards for Hazardous 

Air Pollutants for Industrial, Commercial, and 

Institutional Boilers and Process Heaters

Sec.

What this Subpart Covers

63.7480 What is the purpose of this subpart?

63.7485 Am I subject to this subpart?

63.7490 What is the affected source of this subpart?

63.7491 Are any boilers or process heaters not subject to 

this subpart?

63.7495 When do I have to comply with this subpart?

Emission Limitations and Work Practice Standards

63.7499 What are the subcategories of boilers and process 

heaters?

63.7500 What emission limitations, work practice

standards, and operating limits must I meet?

General Compliance Requirements

63.7505 What are my general requirements for complying 

with this subpart?
199

Testing, Fuel Analyses, and Initial Compliance Requirements

63.7510 What are my initial compliance requirements and 

by what date must I conduct them?

63.7515 When must I conduct subsequent performance tests

or fuel analyses?

63.7520 What stack tests and procedures must I use for 

the performance tests?

63.7521 What fuel analyses and procedures must I use for 

the performance tests?

63.7522 Can I use emission averaging to comply with this 

subpart?

63.7525 What are my monitoring, installation, operation, 

and maintenance requirements?

63.7530 How do I demonstrate initial compliance with the 

emission limitations and work practice standards?

Continuous Compliance Requirements

63.7535 How do I monitor and collect data to demonstrate 

continuous compliance?

63.7540 How do I demonstrate continuous compliance with 

the emission limitations and work practice 

standards?

63.7541 How do I demonstrate continuous compliance under 

the emission averaging provision?

Notifications, Reports, and Records

63.7545 What notifications must I submit and when?

63.7550 What reports must I submit and when?

63.7555 What records must I keep?

63.7560 In what form and how long must I keep my records?

Other Requirements and Information

63.7565 What parts of the General Provisions apply to me?

63.7570 Who implements and enforces this subpart?

63.7575 What definitions apply to this subpart?

Tables to Subpart DDDDD of Part 63

Table 1 to Subpart DDDDD of Part 63 - Emission Limits for 

New or Reconstructed Boilers and Process Heaters
200

Table 2 to Subpart DDDDD of Part 63 – Emission Limits for 

Existing Boilers and Process Heaters (Units with heat 

input capacity of 10 million Btu per hour or greater)

Table 3 to Subpart DDDDD of Part 63 - Work Practice 

Standards

Table 4 to Subpart DDDDD of Part 63 – Operating Limits for 

Boilers and Process Heaters

Table 5 to Subpart DDDDD of Part 63 - Performance Testing 

Requirements

Table 6 to Subpart DDDDD of Part 63 – Fuel Analysis 

Requirements

Table 7 to Subpart DDDDD of Part 63 – Establishing 

Operating Limits

Table 8 to Subpart DDDDD of Part 63 – Demonstrating 

Continuous Compliance

Table 9 to Subpart DDDDD of Part 63 – Reporting 

Requirements

Table 10 to Subpart DDDDD of Part 63 - Applicability of 

General Provisions to Subpart DDDDD

WHAT THIS SUBPART COVERS

§63.7480 What is the purpose of this subpart? 

This subpart establishes national emission limitations 

and work practice standards for hazardous air pollutants

(HAP) emitted from industrial, commercial, and 

institutional boilers and process heaters. This subpart 

also establishes requirements to demonstrate initial and 

continuous compliance with the emission limitations and 

work practice standards.

§63.7485 Am I subject to this subpart? 

You are subject to this subpart if you own or operate 

an industrial, commercial, or institutional boiler or 

process heater as defined in §63.7575 that is located at, 

or is part of, a major source of HAP as defined in §63.2 or 
201

§63.761 (40 CFR part 63, subpart HH, National Emission 

Standards for Hazardous Air Pollutants from Oil and Natural 

Gas Production Facilities), except as specified in 

§63.7491. 

§ 63.7490 What is the affected source of this subpart?

(a) This subpart applies to new, reconstructed, and

existing affected sources as described in paragraphs (a)(1) 

and (2) of this section.

(1) The affected source of this subpart is the collection 

of all existing industrial, commercial, and institutional 

boilers and process heaters within a subcategory located at 

a major source as defined in §63.7575.

(2) The affected source of this subpart is each new or 

reconstructed industrial, commercial, or institutional 

boiler or process heater located at a major source as 

defined in §63.7575.

(b) A boiler or process heater is new if you commence 

construction of the boiler or process heater after [INSERT 

DATE OF PUBLICATION OF THIS PROPOSED RULE IN THE FEDERAL 

REGISTER], and you meet the applicability criteria at the 

time you commence construction.

(c) A boiler or process heater is reconstructed if you meet 

the reconstruction criteria as defined in §63.2, you 

commence reconstruction after [INSERT DATE OF PUBLICATION 
202

OF THIS PROPOSED RULE IN THE FEDERAL REGISTER], and you 

meet the applicability criteria at the time you commence 

reconstruction.

(d) A boiler or process heater is existing if it is not new 

or reconstructed.

§ 63.7491 Are any boilers or process heaters not subject 

to this subpart?

The types of boilers and process heaters listed in 

paragraphs (a) through (o) of this section are not subject 

to this subpart.

(a) An electric utility steam generating unit.

(b) A recovery boiler or furnace covered by 40 CFR part 63, 

subpart MM.

(c) A boiler or process heater that is used specifically 

for research and development. This does not include units 

that provide heat or steam to a process at a research and 

development facility.

(d) A hot water heater as defined in this subpart.

(e) A refining kettle covered by 40 CFR part 63, subpart X.

(f) An ethylene cracking furnace covered by 40 CFR part 63, 

subpart YY.

(g) Blast furnace stoves as described in the EPA document, 

entitled “National Emission Standards for Hazardous Air 

Pollutants (NESHAP) for Integrated Iron and Steel Plants—
203

Background Information for Proposed Standards,” (EPA–453/R–

01–005).

(i) Any boiler or process heater specifically listed as an 

affected source in another standard(s) under 40 CFR part 

63.

(j) Temporary boilers as defined in this subpart.

(k) Blast furnace gas fuel-fired boilers and process 

heaters as defined in this subpart.

§63.7495 When do I have to comply with this subpart? 

(a) If you have a new or reconstructed boiler or process 

heater, you must comply with this subpart by [DATE THE 

FINAL RULE IS PUBLISHED IN THE FEDERAL REGISTER] or upon 

startup of your boiler or process heater, whichever is 

later.

(b) If you have an existing boiler or process heater, you 

must comply with this subpart no later than [3 YEARS AFTER 

DATE THE FINAL RULE IS PUBLISHED IN THE FEDERAL REGISTER].

(c) If you have an area source that increases its emissions 

or its potential to emit such that it becomes a major 

source of HAP, paragraphs (c)(1) and (2) of this section 

apply to you.

(1) Any new or reconstructed boiler or process heater at 

the existing source must be in compliance with this subpart 

upon startup.
204

(2) Any existing boiler or process heater at the existing 

source must be in compliance with this subpart within 3 

years after the source becomes a major source.

(d) You must meet the notification requirements in §63.7545 

according to the schedule in §63.7545 and in subpart A of 

this part. Some of the notifications must be submitted 

before you are required to comply with the emission limits 

and work practice standards in this subpart.

EMISSION LIMITATIONS AND WORK PRACTICE STANDARDS

§ 63.7499 What are the subcategories of boilers and 

process heaters?

The subcategories of boilers and process heaters are:

(1) Pulverized coal units,

(2) Stokers designed to burn coal,

(3) Fluidized bed units designed to burn coal,

(4) Stokers designed to burn biomass,

(5) Fluidized bed units designed to burn biomass,

(6) Suspension burners/Dutch Ovens designed to burn 

biomass,

(7) Fuel Cells designed to burn biomass,

(8) Units designed to burn liquid fuel,

(9) Units designed to burn natural gas/refinery gas, and 

(10) Units designed to burn other gases.

Each subcategory is defined in §63.7575.
205

§ 63.7500 What emission limits, work practice standards, 

and operating limits must I meet?

(a) You must meet the requirements in paragraphs 

(a)(1) and (2) of this section. You must meet these 

requirements at all times.

(1) You must meet each emission limit and work 

practice standard in Table 1 through 3 to this subpart that 

applies to your boiler or process heater, for each boiler 

or process heater at your source, except as provided under 

§63.7522.

(2) You must meet each operating limit in Table 4 to 

this subpart that applies to your boiler or process heater. 

If you use a control device or combination of control 

devices not covered in Table 4 to this subpart, or you wish 

to establish and monitor an alternative operating limit and 

alternative monitoring parameters, you must apply to the 

United States Environmental Protection Agency (EPA) 

Administrator for approval of alternative monitoring under 

§63.8(f).

(b) As provided in §63.6(g), EPA may approve use of an 

alternative to the work practice standards in this section.

GENERAL COMPLIANCE REQUIREMENTS

§63.7505 What are my general requirements for complying 

with this subpart?
206

(a) You must be in compliance with the emission 

limits and operating limits in this subpart. These limits

apply to you at all times.

(b) At all times you must operate and maintain any 

affected source, including associated air pollution control 

equipment and monitoring equipment, in a manner consistent 

with safety and good air pollution control practices for 

minimizing emissions. The general duty to minimize 

emissions does not require you to make any further efforts 

to reduce emissions if levels required by this standard 

have been achieved. Determination of whether such 

operation and maintenance procedures are being used will be 

based on information available to the Administrator which 

may include, but is not limited to, monitoring results, 

review of operation and maintenance procedures, review of 

operation and maintenance records, and inspection of the 

source.

(c) You can demonstrate compliance with the applicable 

emission limit for HCl or mercury using fuel analysis if 

the emission rate calculated according to §63.7530(d) is 

less than the applicable emission limit. Otherwise, you 

must demonstrate compliance for HCl or mercury using 

performance stack testing. You must demonstrate compliance 

with all other applicable limits using performance stack 
207

testing, or the continuous monitoring system (CMS) where 

applicable.

(d) If you demonstrate compliance with any applicable 

emission limit through performance stack testing, you must 

develop a site-specific monitoring plan according to the 

requirements in paragraphs (d)(1) through (4) of this 

section. This requirement also applies to you if you 

petition the EPA Administrator for alternative monitoring 

parameters under §63.8(f).

(1) For each continuous monitoring system (CMS) 

required in this section, you must develop, and submit to 

the permitting authority for approval upon request, a sitespecific monitoring plan that addresses paragraphs 

(d)(1)(i) through (iii) of this section. You must submit 

this site-specific monitoring plan, if requested, at least 

60 days before your initial performance evaluation of your 

CMS.

(i) Installation of the CMS sampling probe or other 

interface at a measurement location relative to each 

affected process unit such that the measurement is 

representative of control of the exhaust emissions (e.g., 

on or downstream of the last control device);

(ii) Performance and equipment specifications for the 

sample interface, the pollutant concentration or parametric 
208

signal analyzer, and the data collection and reduction 

systems; and

(iii) Performance evaluation procedures and acceptance 

criteria (e.g., calibrations).

(2) In your site-specific monitoring plan, you must 

also address paragraphs (d)(2)(i) through (iii) of this 

section.

(i) Ongoing operation and maintenance procedures in 

accordance with the general requirements of §63.8(c)(1)(i) 

and (ii), (c)(3), and (c)(4)(ii);

(ii) Ongoing data quality assurance procedures in 

accordance with the general requirements of §63.8(d); and

(iii) Ongoing recordkeeping and reporting procedures 

in accordance with the general requirements of §63.10(c), 

(e)(1), and (e)(2)(i).

(3) You must conduct a performance evaluation of each 

CMS in accordance with your site-specific monitoring plan.

(4) You must operate and maintain the CMS in 

continuous operation according to the site-specific 

monitoring plan.

TESTING, FUEL ANALYSES, AND INITIAL COMPLIANCE REQUIREMENTS

§ 63.7510 What are my initial compliance requirements and 

by what date must I conduct them?
209

(a) For affected sources that elect to demonstrate 

compliance with any of the emission limits of this subpart 

through performance stack testing, your initial compliance 

requirements include conducting performance stack tests 

according to §63.7520 and Table 5 to this subpart, 

conducting a fuel analysis for each type of fuel burned in 

your boiler or process heater according to §63.7521 and 

Table 6 to this subpart, establishing operating limits 

according to §63.7530 and Table 7 to this subpart, and 

conducting CMS performance evaluations according to 

§63.7525. For affected sources that burn a single type of 

fuel, you are exempted from the initial compliance 

requirements of conducting a fuel analysis for each type of 

fuel burned in your boiler or process heater according to 

§63.7521 and Table 6 to this subpart.

(b) For affected sources that elect to demonstrate 

compliance with the emission limits for HCl or mercury 

through fuel analysis, your initial compliance requirement 

is to conduct a fuel analysis for each type of fuel burned 

in your boiler or process heater according to §63.7521 and 

Table 6 to this subpart and establish operating limits 

according to §63.7530 and Table 8 to this subpart.

(c) If your boiler or process heater has a heat input 

capacity less than 100 MMBtu per hour, your initial 
210

compliance demonstration is conducting a performance stack 

test for CO according to Table 5 to this subpart. If your 

boiler or process heater has a heat input capacity of 100 

MMBtu per hour or greater, your initial compliance 

demonstration is conducting a performance evaluation of 

your continuous emission monitoring system for CO according 

to §63.7525(a).

(d) If your boiler or process heater has a heat input 

capacity of 250 MMBtu per hour or greater and combust coal, 

biomass, or residual oil, your initial compliance 

demonstration is conducting a performance evaluation of 

your continuous emission monitoring system for PM according 

to §63.7525(b).

(e) For existing affected sources, you must 

demonstrate initial compliance no later than 180 days after 

the compliance date that is specified for your source in 

§63.7495 and according to the applicable provisions in 

§63.7(a)(2) as cited in Table 10 to this subpart.

(f) If your new or reconstructed affected source 

commenced construction or reconstruction between [INSERT 

DATE OF PUBLICATION OF THIS PROPOSED RULE IN THE FEDERAL 

REGISTER] and [INSERT DATE 60 DAYS AFTER PUBLICATION OF THE 

FINAL RULE IN THE FEDERAL REGISTER], you must demonstrate 

initial compliance with either the proposed emission limits
211

or the promulgated emission limits no later than 180 days 

after [INSERT DATE 60 DAYS AFTER PUBLICATION OF THE FINAL 

RULE IN THE FEDERAL REGISTER] or within 180 days after 

startup of the source, whichever is later, according to

§63.7(a)(2)(ix).

(g) If your new or reconstructed affected source 

commenced construction or reconstruction between [INSERT 

DATE OF PUBLICATION OF THIS PROPOSED RULE IN THE FEDERAL 

REGISTER], and [INSERT DATE 60 DAYS AFTER PUBLICATION OF 

THE FINAL RULE IN THE FEDERAL REGISTER], and you chose to 

comply with the proposed emission limits when demonstrating 

initial compliance, you must conduct a second compliance 

demonstration for the promulgated emission limits within 3 

years after [INSERT DATE 60 DAYS AFTER PUBLICATION OF THE 

FINAL RULE IN THE FEDERAL REGISTER] or within 3 years after

startup of the affected source, whichever is later.

(h) If your new or reconstructed affected source 

commences construction or reconstruction after [INSERT DATE 

60 DAYS AFTER PUBLICATION OF THE FINAL RULE IN THE FEDERAL 

REGISTER], you must demonstrate initial compliance with the 

promulgated emission limits no later than 180 days after 

startup of the source.

§ 63.7515 When must I conduct subsequent performance 

tests or fuel analyses?
212

(a) You must conduct all applicable performance tests 

according to §63.7520 on an annual basis, unless you follow 

the requirements listed in paragraphs (b) through (e) of 

this section. Annual performance tests must be completed 

between 10 and 12 months after the previous performance 

test, unless you follow the requirements listed in 

paragraphs (b) through (e) of this section.

(b) You can conduct performance stack tests less often 

for a given pollutant if your performance stack tests for 

the pollutant for at least 3 consecutive years show that 

your emissions are at or below 75 percent of the emission 

limit, and if there are no changes in the operation of the 

affected source or air pollution control equipment that 

could increase emissions. In this case, you do not have to 

conduct a performance test for that pollutant for the next 

2 years. You must conduct a performance test during the 

third year and no more than 36 months after the previous 

performance test. This reduced testing option does not 

apply to performance stack tests for dioxin/furan. If you 

elect to demonstrate compliance using emission averaging 

under §63.7522, you must continue to conduct performance 

stack tests annually. 

(c) If your boiler or process heater continues to 

meet the emission limit for the pollutant, you may choose 
213

to conduct performance stack tests for the pollutant every 

third year if your emissions are at or below 75 percent of 

the emission limit, and if there are no changes in the 

operation of the affected source or air pollution control 

equipment that could increase emissions, but each such 

performance test must be conducted no more than 36 months 

after the previous performance test. This reduced testing 

option does not apply to performance stack tests for 

dioxin/furan. If you elect to demonstrate compliance using 

emission averaging under §63.7522, you must continue to 

conduct performance stack tests annually.

(d) If a performance test shows emissions exceeded 75

percent of the emission limit, you must conduct annual 

performance tests for that pollutant until all performance 

tests over a consecutive 3-year period show compliance.

(e) If you are required to meet an applicable work 

practice standard, you must conduct annual performance 

tune-ups according to §63.7520. Each annual tune-up must 

be conducted between 10 and 12 months after the previous 

tune-up.

(f) If you demonstrate compliance with the mercury or 

HCl based on fuel analysis, you must conduct a fuel 

analysis according to §63.7521 for each type of fuel burned 

monthly. If you burn a new type of fuel, you must conduct 
214

a fuel analysis before burning the new type of fuel in your 

boiler or process heater. You must still meet all 

applicable continuous compliance requirements in §63.7540.

(g) You must report the results of performance tests

(stack test and fuel analyses) within 60 days after the 

completion of the performance tests. This report must also 

verify that the operating limits for your affected source 

have not changed or provide documentation of revised 

operating parameters established according to §63.7530 and 

Table 7 to this subpart, as applicable. The reports for 

all subsequent performance tests must include all 

applicable information required in §63.7550.

§ 63.7520 What stack tests and procedures must I use for 

the performance tests?

(a) You must conduct all performance tests according 

to §63.7(c), (d), (f), and (h). You must also develop a 

site-specific test plan according to the requirements in 

§63.7(c).

(b) You must conduct each performance test according 

to the requirements in Table 5 to this subpart.

(c) You must conduct each performance stack test under 

the specific conditions listed in Tables 5 and 7 to this 

subpart. You must conduct performance stack tests at the 

maximum normal operating load while burning the type of 
215

fuel or mixture of fuels that has the highest content of 

chlorine and mercury, and you must demonstrate initial 

compliance and establish your operating limits based on 

these tests. These requirements could result in the need to 

conduct more than one performance test.

(d) You must conduct three separate test runs for each 

performance test required in this section, as specified in 

§63.7(e)(3). Each test run must last at least 4 hours.

(e) To determine compliance with the emission limits, 

you must use the F-Factor methodology and equations in 

sections 12.2 and 12.3 of EPA Method 19 of appendix A to 

part 60 of this chapter to convert the measured particulate 

matter concentrations, the measured HCl concentrations, and 

the measured mercury concentrations that result from the 

initial performance test to pounds per million Btu heat 

input emission rates using F-factors.

§ 63.7521 What fuel analyses and procedures must I use

for the performance tests?

(a) You must conduct performance fuel analysis tests 

according to the procedures in paragraphs (b) through (e) 

of this section and Table 6 to this subpart, as applicable.

(b) You must develop and submit a site-specific fuel 

analysis plan to the EPA Administrator for review and 
216

approval according to the following procedures and 

requirements in paragraphs (b)(1) and (2) of this section.

(1) You must submit the fuel analysis plan no later 

than 60 days before the date that you intend to demonstrate 

compliance.

(2) You must include the information contained in 

paragraphs (b)(2)(i) through (vi) of this section in your 

fuel analysis plan.

(i) The identification of all fuel types anticipated 

to be burned in each boiler or process heater.

(ii) For each fuel type, the notification of whether 

you or a fuel supplier will be conducting the fuel 

analysis.

(iii) For each fuel type, a detailed description of 

the sample location and specific procedures to be used for 

collecting and preparing the composite samples if your 

procedures are different from paragraph (c) or (d) of this 

section. Samples should be collected at a location that 

most accurately represents the fuel type, where possible, 

at a point prior to mixing with other dissimilar fuel 

types.

(iv) For each fuel type, the analytical methods from 

Table 6, with the expected minimum detection levels, to be 

used for the measurement of chlorine or mercury.
217

(v) If you request to use an alternative analytical 

method other than those required by Table 6 to this 

subpart, you must also include a detailed description of 

the methods and procedures that you are proposing to use. 

Methods in Table 6 shall be used until the requested 

alternative is approved.

(vi) If you will be using fuel analysis from a fuel 

supplier in lieu of site-specific sampling and analysis, 

the fuel supplier must use the analytical methods required 

by Table 6 to this subpart.

(c) At a minimum, you must obtain three composite fuel 

samples for each fuel type according to the procedures in 

paragraph (c)(1) or (2) of this section.

(1) If sampling from a belt (or screw) feeder, collect fuel 

samples according to paragraphs (c)(1)(i) and (ii) of this 

section.

(i) Stop the belt and withdraw a 6-inch wide sample 

from the full cross-section of the stopped belt to obtain a 

minimum two pounds of sample. You must collect all the 

material (fines and coarse) in the full cross-section. You 

must transfer the sample to a clean plastic bag.

(ii) Each composite sample will consist of a minimum 

of three samples collected at approximately equal 1-hour 

intervals during the testing period.
218

(2) If sampling from a fuel pile or truck, you must 

collect fuel samples according to paragraphs (c)(2)(i) 

through (iii) of this section.

(i) For each composite sample, you must select a 

minimum of five sampling locations uniformly spaced over 

the surface of the pile.

(ii) At each sampling site, you must dig into the pile 

to a depth of 18 inches. You must insert a clean flat 

square shovel into the hole and withdraw a sample, making 

sure that large pieces do not fall off during sampling.

(iii) You must transfer all samples to a clean plastic 

bag for further processing.

(d) You must prepare each composite sample according 

to the procedures in paragraphs (d)(1) through (7) of this 

section.

(1) You must thoroughly mix and pour the entire 

composite sample over a clean plastic sheet.

(2) You must break sample pieces larger than 3 inches 

into smaller sizes.

(3) You must make a pie shape with the entire 

composite sample and subdivide it into four equal parts.

(4) You must separate one of the quarter samples as 

the first subset.
219

(5) If this subset is too large for grinding, you must 

repeat the procedure in paragraph (d)(3) of this section 

with the quarter sample and obtain a one-quarter subset 

from this sample.

(6) You must grind the sample in a mill.

(7) You must use the procedure in paragraph (d)(3) of 

this section to obtain a one-quarter subsample for 

analysis. If the quarter sample is too large, subdivide it 

further using the same procedure.

(e) You must determine the concentration of pollutants 

in the fuel (mercury and/or chlorine) in units of pounds 

per million Btu of each composite sample for each fuel type 

according to the procedures in Table 6 to this subpart.

§ 63.7522 Can I use emission averaging to comply with 

this subpart?

(a) As an alternative to meeting the requirements of 

§63.7500 for particulate matter, HCl, or mercury on a 

boiler or process heater-specific basis, if you have more 

than one existing boiler or process heater in any 

subcategory located at your facility, you may demonstrate 

compliance by emission averaging, if your averaged 

emissions are within 90 percent of the applicable emission 

limit, according to the procedures in this section.
220

(b) Separate stack requirements. For a group of two 

or more existing boilers or process heaters in the same 

subcategory that each vent to a separate stack, you may 

average particulate matter, HCl, and mercury emissions to 

demonstrate compliance with the limits in Table 2 to this 

subpart if you satisfy the requirements in paragraphs (c), 

(d), (e), (f), and (g) of this section.

(c) For each existing boiler or process heater in the 

averaging group, the emission rate achieved during the 

initial compliance test for the HAP being averaged must not 

exceed the emission level that was being achieved on 

[INSERT THE DATE 30 DAYS AFTER PUBLICATION OF THE FINAL 

RULE IN THE FEDERAL REGISTER] or the control technology 

employed during the initial compliance test must not be 

less effective for the HAP being averaged than the control 

technology employed on [INSERT THE DATE 30 DAYS AFTER 

PUBLICATION OF THE FINAL RULE IN THE FEDERAL REGISTER] .

(d) The averaged emissions rate from the existing 

boilers and process heaters participating in the emissions 

averaging option must be in compliance with the limits in 

Table 2 to this subpart at all times following the 

compliance date specified in §63.7495.

(e) You must demonstrate initial compliance according 

to paragraph (e)(1) or (2) of this section.
221

(1) You must use Equation 1 of this section to 

demonstrate that the particulate matter, HCl, and mercury 

emissions from all existing units participating in the 

emissions averaging option do not exceed the emission 

limits in Table 2 to this subpart.

Where:

Ave Weighted Emissions = Average weighted emissions 

for particulate matter, HCl, or mercury, in units of pounds 

per million Btu of heat input.

Er = Emission rate (as calculated according to Table 5 

to this subpart for particulate matter, HCl, or mercury or 

by fuel analysis for HCl or mercury as calculated by the 

applicable equation in §63.7530(c)) for unit, i, for 

particulate matter, HCl, or mercury, in units of pounds per 

million Btu of heat input.

Hm = Maximum rated heat input capacity of unit, i, in 

units of million Btu per hour.

n = Number of units participating in the emissions 

averaging option.

0.90 = Required discount factor.

(2) If you are not capable of monitoring heat input, 

and the boiler generates steam, you may use Equation 2 of 

this section as an alternative to using Equation 1 of this 

section to demonstrate that the particulate matter, HCl, 

and mercury emissions from all existing units participating 
222

in the emissions averaging option do not exceed the 

emission limits in Table 2 to this subpart.

Where:

Ave Weighted Emissions = Average weighted emission 

level for PM, HCl, or mercury, in units of pounds per 

million Btu of heat input.

Er = Emission rate (as calculated according to Table 5 

to this subpart for particulate matter, HCl, or mercury or 

by fuel analysis for HCl or mercury as calculated by the 

applicable equation in §63.7530(c)) for unit, i, for 

particulate matter, HCl, or mercury, in units of pounds per 

million Btu of heat input.

Sm = Maximum steam generation by unit, i, in units of 

pounds.

Cf = Conversion factor, calculated from the most 

recent compliance test, in units of million Btu of heat 

input per pounds of steam generated for unit, i.

0.90 = Required discount factor.

(f) You must demonstrate compliance on a monthly basis 

determined at the end of every month (12 times per year) 

according to paragraphs (f)(1) through (3) of this section. 

The first monthly period begins on the compliance date 

specified in §63.7495.

(1) For each calendar month, you must use Equation 3 

of this section to calculate the monthly average weighted 

emission rate using the actual heat capacity for each 

existing unit participating in the emissions averaging 

option.
223

Where:

Ave Weighted Emissions = monthly average weighted 

emission level for particulate matter, HCl, or mercury, in 

units of pounds per million Btu of heat input.

Er = Emission rate, (as calculated during the most 

recent compliance test, (as calculated according to Table 5 

to this subpart for particulate matter, HCl, or mercury or 

by fuel analysis for HCl or mercury as calculated by the 

applicable equation in §63.7530(c)) for unit, i, for 

particulate matter, HCl, or mercury, in units of pounds per 

million Btu of heat input.

Hb = The average heat input for each calendar month of 

boiler, i, in units of million Btu.

n = Number of units participating in the emissions 

averaging option.

0.90 = Required discount factor.

(2) If you are not capable of monitoring heat input, 

you may use Equation 4 of this section as an alternative to 

using Equation 3 of this section to calculate the monthly 

weighted emission rate using the actual steam generation 

from the units participating in the emissions averaging 

option.

Where:

Ave Weighted Emissions = monthly average weighted 

emission level for PM, HCl, or mercury, in units of pounds 

per million Btu of heat input.
224

Er = Emission rate, (as calculated during the most 

recent compliance test (as calculated according to Table 5 

to this subpart for particulate matter, HCl, or mercury or 

by fuel analysis for HCl or mercury as calculated by the 

applicable equation in §63.7530(c)) for unit, i, for 

particulate matter, HCl, or mercury, in units of pounds per 

million Btu of heat input.

Sa = Actual steam generation for each calendar month 

by boiler, i, in units of pounds.

Cf = Conversion factor, as calculated during the most 

recent compliance test, in units of million Btu of heat 

input per pounds of steam generated for unit, i.

0.90 = Required discount factor.

(3) Until 12 monthly weighted average emission rates 

have been accumulated, calculate and report only the 

monthly average weighted emission rate determined under 

paragraph (f)(1) or (2) of this section. After 12 monthly 

weighted average emission rates have been accumulated, for 

each subsequent calendar month, use Equation 5 of this 

section to calculate the 12-month rolling average of the 

monthly weighted average emission rates for the current 

month and the previous 11 months.

Where:

Eavg = 12-month rolling average emission rate, (pounds 

per million Btu heat input)

ERi = Monthly weighted average, for month “i”, (pounds 

per million Btu heat input)(as calculated by (f)(1) or (2))

(g) You must develop, and submit to the applicable 

regulatory authority for review and approval upon request, 
225

an implementation plan for emission averaging according to 

the following procedures and requirements in paragraphs 

(g)(1) through (4).

(1) You must submit the implementation plan no later 

than 180 days before the date that the facility intends to 

demonstrate compliance using the emission averaging option.

(2) You must include the information contained in 

paragraphs (g)(2)(i) through (vii) of this section in your 

implementation plan for all emission sources included in an 

emissions average:

(i) The identification of all existing boilers and 

process heaters in the averaging group, including for each 

either the applicable HAP emission level or the control

technology installed as of [INSERT DATE 60 DAYS AFTER 

PUBLICATION OF THE FINAL RULE IN THE FEDERAL REGISTER] and 

the date on which you are requesting emission averaging to 

commence;

(ii) The process parameter (heat input or steam 

generated) that will be monitored for each averaging group;

(iii) The specific control technology or pollution 

prevention measure to be used for each emission boiler or 

process heater in the averaging group and the date of its 

installation or application. If the pollution prevention 

measure reduces or eliminates emissions from multiple 
226

boilers or process heaters, the owner or operator must 

identify each boiler or process heater;

(iv) The test plan for the measurement of particulate 

matter, HCl, or mercury emissions in accordance with the 

requirements in §63.7520;

(v) The operating parameters to be monitored for each 

control system or device consistent with 63.7500 and Table 

4, and a description of how the operating limits will be 

determined;

(vi) If you request to monitor an alternative 

operating parameter pursuant to §63.7525, you must also 

include:

(A) A description of the parameter(s) to be monitored 

and an explanation of the criteria used to select the 

parameter(s); and

(B) A description of the methods and procedures that

will be used to demonstrate that the parameter indicates 

proper operation of the control device; the frequency and 

content of monitoring, reporting, and recordkeeping 

requirements; and a demonstration, to the satisfaction of 

the applicable regulatory authority, that the proposed 

monitoring frequency is sufficient to represent control 

device operating conditions; and
227

(vii) A demonstration that compliance with each of the 

applicable emission limit(s) will be achieved under 

representative operating conditions.

(3) The regulatory authority shall review and approve 

or disapprove the plan according to the following criteria:

(i) Whether the content of the plan includes all of 

the information specified in paragraph (g)(2) of this 

section; and

(ii) Whether the plan presents sufficient information 

to determine that compliance will be achieved and 

maintained.

(4) The applicable regulatory authority shall not 

approve an emission averaging implementation plan 

containing any of the following provisions:

(i) Any averaging between emissions of differing 

pollutants or between differing sources; or

(ii) The inclusion of any emission source other than 

an existing unit in the same subcategory.

(h) Common stack requirements. For a group of two or 

more existing affected units, each of which vents through a 

single common stack, you may average particulate matter, 

HCl and mercury emissions to demonstrate compliance with 

the limits in Table 2 to this subpart if you satisfy the 

requirements in paragraph (i) or (j) of this section.
228

(i) For a group of two or more existing units in the 

same subcategory, each of which vents through a common 

emissions control system to a common stack, that does not 

receive emissions from units in other subcategories or 

categories, you may treat such averaging group as a single 

existing unit for purposes of this subpart and comply with 

the requirements of this subpart as if the group were a 

single unit.

(j) For all other groups of units subject to paragraph 

(h) of this section, the owner or operator may elect to:

(1) Conduct performance tests according to procedures 

specified in §63.7520 in the common stack if affected units 

from other subcategories vent to the common stack. The 

emission limits that the group must comply with are 

determined by the use of equation 6.

Where:

En= HAP emission limit, lb/MMBtu, ppm, or ng/dscm;

ELi= Appropriate emission limit from Table 2 to this subpart

for unit i, in units of lb/MMBtu, ppm or ng/dscm;

Hi= Heat input from unit i, MMBtu;
229

(2) Conduct performance tests according to procedures 

specified in §63.7520 in the common stack. If affected 

units from nonaffected units vent to the common stack, the 

units from nonaffected units must be shut down or vented to 

a different stack during the performance test); and

(3) Meet the applicable operating limit specified in 

§63.7540 and Table 8 to this subpart for each emissions 

control system (except that, if each unit venting to the 

common stack has an applicable opacity operating limit, 

then a single continuous opacity monitoring system may be 

located in the common stack instead of in each duct to the 

common stack).

(k) Combination requirements. The common stack of a 

group of two or more existing boilers or process heaters in 

the same subcategory subject to paragraph (h) of this 

section may be treated as a separate stack for purposes of 

paragraph (b) of this section and included in an emissions 

averaging group subject to paragraph (b) of this section.

§ 63.7525 What are my monitoring, installation, 

operation, and maintenance requirements?

(a) If your boiler or process heater has a heat input 

capacity of 100 MMBtu per hour or greater, you must 

install, operate, and maintain a continuous emission 

monitoring system (CEMS) for CO and oxygen according to the 
230

procedures in paragraphs (a)(1) through (6) of this section 

by the compliance date specified in §63.7495. The CO and 

oxygen shall be monitored at the same location at the 

outlet of the boiler or process heater.

(1) Each CEMS must be installed, operated, and 

maintained according to the applicable procedures under 

Performance Specification (PS) 3 or 4A of 40 CFR part 60, 

appendix B, and according to the site-specific monitoring 

plan developed according to §63.7505(d).

(2) You must conduct a performance evaluation of each 

CEMS according to the requirements in §63.8 and according 

to PS 4A of 40 CFR part 60, appendix B.

(3) Each CEMS must complete a minimum of one cycle of 

operation (sampling, analyzing, and data recording) for 

each successive 15-minute period.

(4) The CEMS data must be reduced as specified in 

§63.8(g)(2).

(5) You must calculate and record a 30-day rolling 

average emission rate on a daily basis. A new 30-day 

rolling average emission rate is calculated as the average 

of all of the hourly CO emission data for the preceding 30 

operating days.

(6) For purposes of calculating data averages, you 

must use all the data collected during all periods in 
231

assessing compliance. Any period for which the monitoring 

system is out of control and data are not available for

required calculations constitutes a deviation from the 

monitoring requirements.

(b) If your boiler or process heater has a heat input 

capacity of 250 MMBtu per hour or greater and combusts

coal, biomass, or residual oil, you must install, certify,

maintain, and operate a CEMS measuring PM emissions 

discharged to the atmosphere and record the output of the

system as specified in paragraphs (b)(1) through (b)(6) of 

this section.

(1) Each CEMS shall be installed, certified, operated, 

and maintained according to the requirements in

§63.7540(a)(8).

(2) The initial performance evaluation shall be 

completed no later than 180 days after the date of initial 

startup of a new unit or within 180 days of the compliance 

date for an existing unit, as specified under §63.7495 of 

this subpart.

(3) Compliance with the applicable emissions limit 

shall be determined based on the 24-hour daily (block)

average of the hourly arithmetic average emissions 

concentrations using the continuous monitoring system 

outlet data. The 24-hour block arithmetic average emission 
232

concentration shall be calculated using EPA Reference 

Method 19 of appendix A of 40 CFR part 60.

(4) Obtain valid CEMS hourly averages for all 

operating hours on a 30-day rolling average basis. At 

least two data points per hour shall be used to calculate 

each 1-hour arithmetic average.

(5) The 1-hour arithmetic averages required shall be 

expressed in lb/MMBtu and shall be used to calculate the 

boiler operating day daily arithmetic average emissions.

(6) When PM emissions data are not obtained because of 

CEMS breakdowns, repairs, calibration checks, and zero and

span adjustments, emissions data shall be obtained by using 

other monitoring systems as approved by the Administrator 

or EPA Reference Method 19 of appendix A of 40 CFR part 60 

to provide, as necessary, valid emissions data for all 

operating hours per 30-day rolling average.

(c) If you have an applicable opacity operating limit, 

you must install, operate, certify and maintain each 

continuous opacity monitoring system (COMS) according to 

the procedures in paragraphs (c)(1) through (7) of this 

section by the compliance date specified in §63.7495.

(1) Each COMS must be installed, operated, and 

maintained according to PS 1 of 40 CFR part 60, appendix B.
233

(2) You must conduct a performance evaluation of each 

COMS according to the requirements in §63.8 and according 

to PS 1 of 40 CFR part 60, appendix B.

(3) As specified in §63.8(c)(4)(i), each COMS must 

complete a minimum of one cycle of sampling and analyzing 

for each successive 10-second period and one cycle of data 

recording for each successive 6-minute period.

(4) The COMS data must be reduced as specified in 

§63.8(g)(2).

(5) You must include in your site-specific monitoring 

plan procedures and acceptance criteria for operating and 

maintaining each COMS according to the requirements in 

§63.8(d). At a minimum, the monitoring plan must include a 

daily calibration drift assessment, a quarterly performance 

audit, and an annual zero alignment audit of each COMS.

(6) You must operate and maintain each COMS according 

to the requirements in the monitoring plan and the 

requirements of §63.8(e). You must identify periods the 

COMS is out of control including any periods that the COMS 

fails to pass a daily calibration drift assessment, a 

quarterly performance audit, or an annual zero alignment 

audit. Any 6-minute period for which the monitoring system 

is out of control and data are not available for required 
234

calculations constitutes a deviation from the monitoring 

requirements.

(7) You must determine and record all the 6-minute 

averages (and 1-hour block averages as applicable) 

collected for periods during which the COMS is not out of 

control.

(d) If you have an operating limit that requires the 

use of a CMS, you must install, operate, and maintain each 

continuous parameter monitoring system (CPMS) according to 

the procedures in paragraphs (d)(1) through (5) of this 

section by the compliance date specified in §63.7495.

(1) The CPMS must complete a minimum of one cycle of 

operation for each successive 15-minute period. You must 

have a minimum of four successive cycles of operation to 

have a valid hour of data.

(2) Except for monitoring malfunctions, associated 

repairs, and required quality assurance or control 

activities (including, as applicable, calibration checks 

and required zero and span adjustments), you must conduct 

all monitoring in continuous operation at all times that 

the unit is operating. A monitoring malfunction is any 

sudden, infrequent, not reasonably preventable failure of 

the monitoring to provide valid data. Monitoring failures 
235

that are caused in part by poor maintenance or careless 

operation are not malfunctions.

(3) For purposes of calculating data averages, you 

must not use data recorded during monitoring malfunctions, 

associated repairs, out of control periods, or required 

quality assurance or control activities. You must use all 

the data collected during all other periods in assessing 

compliance. Any 15-minute period for which the monitoring 

system is out-of-control and data are not available for 

required calculations constitutes a deviation from the 

monitoring requirements.

(4) You must determine the 3-hour block average of all 

recorded readings, except as provided in paragraph (c)(3) 

of this section.

(5) You must record the results of each inspection, 

calibration, and validation check.

(e) If you have an operating limit that requires the 

use of a flow measurement device, you must meet the 

requirements in paragraphs (d) and (e)(1) through (4) of 

this section.

(1) You must locate the flow sensor and other 

necessary equipment in a position that provides a 

representative flow.
236

(2) You must use a flow sensor with a measurement 

sensitivity of 2 percent of the flow rate.

(3) You must reduce swirling flow or abnormal velocity 

distributions due to upstream and downstream disturbances.

(4) You must conduct a flow sensor calibration check 

at least semiannually.

(f) If you have an operating limit that requires the 

use of a pressure measurement device, you must meet the 

requirements in paragraphs (d) and (f)(1) through (6) of 

this section.

(1) Locate the pressure sensor(s) in a position that 

provides a representative measurement of the pressure.

(2) Minimize or eliminate pulsating pressure, 

vibration, and internal and external corrosion.

(3) Use a gauge with a minimum tolerance of 1.27 

centimeters of water or a transducer with a minimum 

tolerance of 1 percent of the pressure range.

(4) Check pressure tap pluggage daily.

(5) Using a manometer, you must check gauge 

calibration quarterly and transducer calibration monthly.

(6) Conduct calibration checks any time the sensor 

exceeds the manufacturer's specified maximum operating 

pressure range or install a new pressure sensor.
237

(g) If you have an operating limit that requires the 

use of a pH measurement device, you must meet the 

requirements in paragraphs (d) and (g)(1) through (3) of 

this section.

(1) Locate the pH sensor in a position that provides a 

representative measurement of scrubber effluent pH.

(2) Ensure the sample is properly mixed and 

representative of the fluid to be measured.

(3) Check the pH meter's calibration on at least two 

points every 8 hours of process operation.

(h) If you have an operating limit that requires the 

use of equipment to monitor voltage and secondary amperage

(or total power input) of an electrostatic precipitator 

(ESP), you must use voltage and secondary current 

monitoring equipment to measure voltage and secondary 

current to the ESP.

(i) If you have an operating limit that requires the 

use of equipment to monitor sorbent injection rate ( e.g. , 

weigh belt, weigh hopper, or hopper flow measurement 

device), you must meet the requirements in paragraphs (c) 

and (i)(1) through (3) of this section.

(1) Locate the device in a position(s) that provides a 

representative measurement of the total sorbent injection 

rate.
238

(2) Install and calibrate the device in accordance 

with manufacturer's procedures and specifications.

(3) At least annually, calibrate the device in 

accordance with the manufacturer's procedures and 

specifications.

(j) If you elect to use a fabric filter bag leak 

detection system to comply with the requirements of this 

subpart, you must install, calibrate, maintain, and 

continuously operate a bag leak detection system as 

specified in paragraphs (j)(1) through (8) of this section.

(1) You must install and operate a bag leak detection 

system for each exhaust stack of the fabric filter.

(2) Each bag leak detection system must be installed, 

operated, calibrated, and maintained in a manner consistent 

with the manufacturer's written specifications and 

recommendations and in accordance with the guidance 

provided in EPA–454/R–98–015, September 1997.

(3) The bag leak detection system must be certified by 

the manufacturer to be capable of detecting particulate 

matter emissions at concentrations of 10 milligrams per 

actual cubic meter or less.

(4) The bag leak detection system sensor must provide 

output of relative or absolute particulate matter loadings.
239

(5) The bag leak detection system must be equipped 

with a device to continuously record the output signal from 

the sensor.

(6) The bag leak detection system must be equipped 

with an alarm system that will sound automatically when an 

increase in relative particulate matter emissions over a 

preset level is detected. The alarm must be located where 

it is easily heard by plant operating personnel.

(7) For positive pressure fabric filter systems that 

do not duct all compartments of cells to a common stack, a 

bag leak detection system must be installed in each 

baghouse compartment or cell.

(8) Where multiple bag leak detectors are required, 

the system's instrumentation and alarm may be shared among 

detectors.

§ 63.7530 How do I demonstrate initial compliance with 

the emission limits and work practice standards?

(a) You must demonstrate initial compliance with each 

emission limit that applies to you by conducting initial 

performance tests (performance stack tests and fuel 

analyses) and establishing operating limits, as applicable, 

according to §63.7520, paragraph (c) of this section, and 

Tables 5 and 7 to this subpart.
240

(b) If you demonstrate compliance through performance

stack testing, you must establish each site-specific 

operating limit in Table 2 to this subpart that applies to 

you according to the requirements in §63.7520, Table 7 to 

this subpart, and paragraph (c)(4) of this section, as 

applicable. You must also conduct fuel analyses according 

to §63.7521 and establish maximum fuel pollutant input 

levels according to paragraphs (c)(1) through (3) of this 

section, as applicable.

(1) You must establish the maximum chlorine fuel input 

(Cinput) during the initial performance testing according to 

the procedures in paragraphs (c)(1)(i) through (iii) of 

this section.

(i) You must determine the fuel type or fuel mixture 

that you could burn in your boiler or process heater that 

has the highest content of chlorine.

(ii) During the performance testing for HCl, you must 

determine the fraction of the total heat input for each 

fuel type burned (Qi) based on the fuel mixture that has the 

highest content of chlorine, and the average chlorine 

concentration of each fuel type burned (Ci).

(iii) You must establish a maximum chlorine input 

level using Equation 7 of this section.
241

Where:

Clinput = Maximum amount of chlorine entering the 

boiler or process heater through fuels burned in units of 

pounds per million Btu.

Ci = Arithmetic average concentration of chlorine in 

fuel type, i, analyzed according to §63.7521, in units of 

pounds per million Btu.

Qi = Fraction of total heat input from fuel type, i, 

based on the fuel mixture that has the highest content of 

chlorine. If you do not burn multiple fuel types during the 

performance testing, it is not necessary to determine the 

value of this term. Insert a value of “1” for Qi.

n = Number of different fuel types burned in your 

boiler or process heater for the mixture that has the 

highest content of chlorine.

(2) You must establish the maximum mercury fuel input 

level (Mercuryinput) during the initial performance testing 

using the procedures in paragraphs (c)(3)(i) through (iii) 

of this section.

(i) You must determine the fuel type or fuel mixture 

that you could burn in your boiler or process heater that 

has the highest content of mercury.

(ii) During the compliance demonstration for mercury, 

you must determine the fraction of total heat input for 

each fuel burned (Qi) based on the fuel mixture that has the 

highest content of mercury, and the average mercury 

concentration of each fuel type burned (HGi).
242

(iii) You must establish a maximum mercury input level 

using Equation 8 of this section.

Where:

Mercuryinput= Maximum amount of mercury entering the 

boiler or process heater through fuels burned in units of 

pounds per million Btu.

HGi= Arithmetic average concentration of mercury in 

fuel type, i, analyzed according to §63.7521, in units of 

pounds per million Btu.

Qi= Fraction of total heat input from fuel type, i, 

based on the fuel mixture that has the highest mercury 

content. If you do not burn multiple fuel types during the 

performance test, it is not necessary to determine the 

value of this term. Insert a value of “1” for Qi.

n = Number of different fuel types burned in your 

boiler or process heater for the mixture that has the 

highest content of mercury.

(3) You must establish parameter operating limits 

according to paragraphs (c)(4)(i) through (iv) of this 

section.

(i) For a wet scrubber, you must establish the minimum 

scrubber effluent pH, liquid flowrate, and pressure drop as 

defined in §63.7575, as your operating limits during the 

three-run performance test. If you use a wet scrubber and 

you conduct separate performance tests for particulate 

matter, HCl, and mercury emissions, you must establish one 

set of minimum scrubber effluent pH, liquid flowrate, and 
243

pressure drop operating limits. The minimum scrubber 

effluent pH operating limit must be established during the 

HCl performance test. If you conduct multiple performance 

tests, you must set the minimum liquid flowrate and 

pressure drop operating limits at the highest minimum 

values established during the performance tests.

(ii) For an electrostatic precipitator, you must 

establish the minimum voltage and secondary current (or 

total power input), as defined in §63.7575, as your 

operating limits during the three-run performance test.

(iii) For a dry scrubber, you must establish the 

minimum sorbent injection rate, as defined in §63.7575, as 

your operating limit during the three-run performance test.

(iv) The operating limit for boilers or process 

heaters with fabric filters that choose to demonstrate 

continuous compliance through bag leak detection systems is 

that a bag leak detection system be installed according to 

the requirements in §63.7525, and that each fabric filter 

must be operated such that the bag leak detection system 

alarm does not sound more than 5 percent of the operating 

time during a 6-month period.

(c) If you elect to demonstrate compliance with an 

applicable emission limit through fuel analysis, you must 

conduct fuel analyses according to §63.7521 and follow the 
244

procedures in paragraphs (c)(1) through (5) of this 

section.

(1) If you burn more than one fuel type, you must 

determine the fuel mixture you could burn in your boiler or 

process heater that would result in the maximum emission 

rates of the pollutants that you elect to demonstrate 

compliance through fuel analysis.

(2) You must determine the 90th percentile confidence 

level fuel pollutant concentration of the composite samples 

analyzed for each fuel type using the one-sided z-statistic 

test described in Equation 9 of this section.

Where:

P90= 90th percentile confidence level pollutant 

concentration, in pounds per million Btu.

mean = Arithmetic average of the fuel pollutant 

concentration in the fuel samples analyzed according to 

§63.7521, in units of pounds per million Btu.

SD = Standard deviation of the pollutant concentration 

in the fuel samples analyzed according to §63.7521, in 

units of pounds per million Btu.

t = t distribution critical value for 90th percentile 

(0.1) probability for the appropriate degrees of freedom 

(number of samples minus one) as obtained from a 

Distribution Critical Value Table.

(3) To demonstrate compliance with the applicable 

emission limit for HCl, the HCl emission rate that you 
245

calculate for your boiler or process heater using Equation 

10 of this section must not exceed the applicable emission 

limit for HCl.

Where:

HCl = HCl emission rate from the boiler or process 

heater in units of pounds per million Btu.

Ci90= 90th percentile confidence level concentration of 

chlorine in fuel type, i, in units of pounds per million 

Btu as calculated according to Equation 8 of this section.

Qi= Fraction of total heat input from fuel type, i, 

based on the fuel mixture that has the highest content of 

chlorine. If you do not burn multiple fuel types, it is not 

necessary to determine the value of this term. Insert a 

value of “1” for Qi.

n = Number of different fuel types burned in your 

boiler or process heater for the mixture that has the 

highest content of chlorine.

1.028 = Molecular weight ratio of HCl to chlorine.

(4) To demonstrate compliance with the applicable 

emission limit for mercury, the mercury emission rate that 

you calculate for your boiler or process heater using 

Equation 11 of this section must not exceed the applicable 

emission limit for mercury.

Where:
246

Mercury = Mercury emission rate from the boiler or 

process heater in units of pounds per million Btu.

HGi90= 90th percentile confidence level concentration 

of mercury in fuel, i, in units of pounds per million Btu 

as calculated according to Equation 8 of this section.

Qi= Fraction of total heat input from fuel type, i, 

based on the fuel mixture that has the highest mercury 

content. If you do not burn multiple fuel types, it is not 

necessary to determine the value of this term. Insert a 

value of “1” for Qi.

n = Number of different fuel types burned in your 

boiler or process heater for the mixture that has the 

highest mercury content.

(d) If you own or operate an existing unit with a heat 

input capacity of 10 million Btu per hour or less, you must 

submit a signed statement in the Notification of Compliance 

Status report that indicates that you conducted a tune-up 

of the unit.

(e) You must submit the energy assessment report, 

along with a signed certification that the assessment is an 

accurate depiction of your facility.

(f) You must submit the Notification of Compliance 

Status containing the results of the initial compliance 

demonstration according to the requirements in §63.7545(e).

CONTINUOUS COMPLIANCE REQUIREMENTS

§ 63.7535 How do I monitor and collect data to 

demonstrate continuous compliance?
247

(a) You must monitor and collect data according to 

this section and the site-specific monitoring plan required 

by §63.7505(d).

(b) Except for monitor malfunctions, associated 

repairs, and required quality assurance or control 

activities (including, as applicable, calibration checks 

and required zero and span adjustments), you must monitor 

continuously (or collect data at all required intervals) at 

all times that the affected source is operating.

(c) You may not use data recorded during monitoring 

malfunctions, associated repairs, or required quality 

assurance or control activities in data averages and 

calculations used to report emission or operating levels. 

You must use all the data collected during all other 

periods in assessing the operation of the control device 

and associated control system. 

§ 63.7540 How do I demonstrate continuous compliance with 

the emission limits and work practice standards?

(a) You must demonstrate continuous compliance with 

each emission limit, operating limit, and work practice 

standard in Tables 1 through 3 to this subpart that applies 

to you according to the methods specified in Table 8 to 

this subpart and paragraphs (a)(1) through (10) of this 

section.
248

(1) Following the date on which the initial 

performance test is completed or is required to be 

completed under §§63.7 and 63.7510, whichever date comes 

first, you must not operate above any of the applicable 

maximum operating limits or below any of the applicable 

minimum operating limits listed in Table 4 to this subpart 

at any times. Operation above the established maximum or 

below the established minimum operating limits shall 

constitute a deviation of established operating limits. 

Operating limits must be confirmed or reestablished during 

performance tests.

(2) As specified in §63.7550(c), you must keep records 

of the type and amount of all fuels burned in each boiler 

or process heater during the reporting period to 

demonstrate that all fuel types and mixtures of fuels 

burned would either result in lower emissions of HCl and 

mercury, than the applicable emission limit for each 

pollutant (if you demonstrate compliance through fuel 

analysis), or result in lower fuel input of chlorine and 

mercury than the maximum values calculated during the last 

performance tests (if you demonstrate compliance through 

performance stack testing).

(3) If you demonstrate compliance with an applicable 

HCl emission limit through fuel analysis and you plan to 
249

burn a new type of fuel, you must recalculate the HCl 

emission rate using Equation 9 of §63.7530 according to 

paragraphs (a)(3)(i) through (iii) of this section.

(i) You must determine the chlorine concentration for 

any new fuel type in units of pounds per million Btu, based 

on supplier data or your own fuel analysis, according to 

the provisions in your site-specific fuel analysis plan 

developed according to §63.7521(b).

(ii) You must determine the new mixture of fuels that 

will have the highest content of chlorine.

(iii) Recalculate the HCl emission rate from your 

boiler or process heater under these new conditions using 

Equation 9 of §63.7530. The recalculated HCl emission rate 

must be less than the applicable emission limit.

(4) If you demonstrate compliance with an applicable 

HCl emission limit through performance testing and you plan 

to burn a new type of fuel or a new mixture of fuels, you 

must recalculate the maximum chlorine input using Equation 

5 of §63.7530. If the results of recalculating the maximum 

chlorine input using Equation 5 of §63.7530 are higher than 

the maximum chlorine input level established during the 

previous performance test, then you must conduct a new 

performance test within 60 days of burning the new fuel 

type or fuel mixture according to the procedures in 
250

§63.7520 to demonstrate that the HCl emissions do not 

exceed the emission limit. You must also establish new 

operating limits based on this performance test according 

to the procedures in §63.7530(c).

(5) If you demonstrate compliance with an applicable 

mercury emission limit through fuel analysis, and you plan 

to burn a new type of fuel, you must recalculate the 

mercury emission rate using Equation 11 of §63.7530 

according to the procedures specified in paragraphs 

(a)(7)(i) through (iii) of this section.

(i) You must determine the mercury concentration for 

any new fuel type in units of pounds per million Btu, based 

on supplier data or your own fuel analysis, according to 

the provisions in your site-specific fuel analysis plan 

developed according to §63.7521(b).

(ii) You must determine the new mixture of fuels that 

will have the highest content of mercury.

(iii) Recalculate the mercury emission rate from your 

boiler or process heater under these new conditions using 

Equation 11 of §63.7530. The recalculated mercury emission 

rate must be less than the applicable emission limit.

(6) If you demonstrate compliance with an applicable 

mercury emission limit through performance testing, and you 

plan to burn a new type of fuel or a new mixture of fuels, 
251

you must recalculate the maximum mercury input using 

Equation 7 of §63.7530. If the results of recalculating the 

maximum mercury input using Equation 7 of §63.7530 are 

higher than the maximum mercury input level established 

during the previous performance test, then you must conduct 

a new performance test within 60 days of burning the new 

fuel type or fuel mixture according to the procedures in 

§63.7520 to demonstrate that the mercury emissions do not 

exceed the emission limit. You must also establish new 

operating limits based on this performance test according 

to the procedures in §63.7530(c).

(7) If your unit is controlled with a fabric filter, 

and you demonstrate continuous compliance using a bag leak 

detection system, you must initiate corrective action 

within 1 hour of a bag leak detection system alarm and 

complete corrective actions as soon as practical, and 

operate and maintain the fabric filter system such that the 

alarm does not sound more than 5 percent of the operating 

time during a 6-month period. You must also keep records 

of the date, time, and duration of each alarm, the time 

corrective action was initiated and completed, and a brief 

description of the cause of the alarm and the corrective 

action taken. You must also record the percent of the 

operating time during each 6-month period that the alarm 
252

sounds. In calculating this operating time percentage, if 

inspection of the fabric filter demonstrates that no 

corrective action is required, no alarm time is counted. 

If corrective action is required, each alarm shall be 

counted as a minimum of 1 hour. If you take longer than 1 

hour to initiate corrective action, the alarm time shall be 

counted as the actual amount of time taken to initiate 

corrective action.

(8) If you are required to install a CEMS according to 

§63.7525(a), then you must meet the requirements in 

paragraphs (a)(8)(i) through (iii) of this section.

(i) You must continuously monitor CO according to 

§§63.7525(a) and 63.7535.

(ii) Maintain a CO emission level below or at your 

applicable CO standard in Tables 1 or 2 to this subpart at 

all times.

(iii) Keep records of CO levels according to 

§63.7555(b).

(9) The owner or operator of an affected source using 

a CEMS measuring PM emissions to meet requirements of this 

subpart shall install, certify, operate, and maintain the 

CEMS as specified in paragraphs (a)(9)(i) through 

(a)(9)(iv) of this section.
253

(i) The owner or operator shall conduct a performance 

evaluation of the CEMS according to the applicable

requirements of §60.13 of 40 CFR, Performance Specification 

11 in appendix B of 40 CFR part 60, and procedure 2 in 

appendix F of 40 CFR part 60.

(ii) During each PM correlation testing run of the 

CEMS required by Performance Specification 11 in appendix B 

of 40 CFR part 60, PM and O2 (or CO2) data shall be

collected concurrently (or within a 30-to 60-minute period) 

by both the CEMS and conducting performance tests using 

Method 5 or 5B of appendix A–3 of 40 CFR part 60 or Method 

17 of appendix A–6 of 40 CFR part 60.

(iii) Quarterly accuracy determinations and daily 

calibration drift tests shall be performed in accordance 

with procedure 2 in appendix F of 40 CFR part 60. Relative 

Response Audits must be performed annually and Response

Correlation Audits must be performed every 3 years.

(iv) After December 31, 2011, within 60 days after the date 

of completing each performance evaluation conducted to 

demonstrate compliance with this subpart, the owner or 

operator of the affected facility must submit the test data 

to EPA by successfully entering the data electronically 

into EPA’s WebFIRE database through EPA’s Central Data 

Exchange. The owner or operator of an affected facility 
254

shall enter the test data into EPA’s data base using the 

Electronic Reporting Tool (ERT) or other compatible 

electronic spreadsheet. 

(10) You must conduct a tune-up of the boiler or process 

heater annually to demonstrate continuous compliance as 

specified in paragraphs (a)(10)(i) through (a)(10)(vi) of 

this section.

(i) Inspect the burner, and clean or replace any 

components of the burner as necessary;

(ii) Inspect the flame pattern and make any 

adjustments to the burner necessary to optimize the flame 

pattern consistent with the manufacturer’s specifications;

(iii) Inspect the system controlling the air-to-fuel 

ratio, and ensure that it is correctly calibrated and 

functioning properly;

(iv) Minimize total emissions of CO consistent with 

the manufacturer’s specifications;

(v) Measure the concentration in the effluent stream 

of CO in parts per million, by volume, dry basis (ppmvd), 

before and after the adjustments are made; and

(vi) Maintain on-site and submit, if requested by the 

Administrator, an annual report containing the information 

in paragraphs (b)(6)(i) through (iii) of this section,
255

(i) The concentrations of CO in the effluent stream 

in ppmvd, and oxygen in percent dry basis, measured before 

and after the adjustments of the boiler;

(ii) A description of any corrective actions taken as 

a part of the combustion adjustment; and

(iii) The type and amount of fuel used over the 12 

months prior to the annual adjustment.

(b) You must report each instance in which you did not meet 

each emission limit and operating limit in Tables 1 through 

4 to this subpart that apply to you. These instances are 

deviations from the emission limits in this subpart. These 

deviations must be reported according to the requirements 

in §63.7550.

§ 63.7541 How do I demonstrate continuous compliance 

under the emission averaging provision?

(a) Following the compliance date, the owner or 

operator must demonstrate compliance with this subpart on a 

continuous basis by meeting the requirements of paragraphs 

(a)(1) through (5) of this section.

(1) For each calendar month, demonstrate compliance 

with the average weighted emissions limit for the existing

units participating in the emissions averaging option as 

determined in §63.7522(f) and (g);
256

(2) You must maintain the applicable opacity limit 

according to paragraphs (a)(2)(i) through (ii) of this 

section.

(i) For each existing unit participating in the 

emissions averaging option that is equipped with a dry 

control system and not vented to a common stack, maintain 

opacity at or below the applicable limit.

(ii) For each group of units participating in the 

emissions averaging option where each unit in the group is 

equipped with a dry control system and vented to a common 

stack that does not receive emissions from nonaffected 

units, maintain opacity at or below the applicable limit at 

the common stack;

(3) For each existing unit participating in the 

emissions averaging option that is equipped with a wet 

scrubber, maintain the 3-hour average parameter values at 

or below the operating limits established during the most 

recent performance test; and

(4) For each existing unit participating in the 

emissions averaging option that has an approved alternative 

operating plan, maintain the 3-hour average parameter 

values at or below the operating limits established in the 

most recent performance test.
257

(5) For each existing unit participating in the 

emissions averaging option venting to a common stack 

configuration containing affected units from other 

subcategories, maintain the appropriate operating limit for 

each unit as specified in Table 4 to this subpart that 

applies.

(b) Any instance where the owner or operator fails to 

comply with the continuous monitoring requirements in 

paragraphs (a)(1) through (5) of this section is a 

deviation.

Notification, Reports, and Records

§ 63.7545 What notifications must I submit and when?

(a) You must submit all of the notifications in 

§§63.7(b) and (c), 63.8 (e), (f)(4) and (6), and 63.9 (b) 

through (h) that apply to you by the dates specified.

(b) As specified in §63.9(b)(2), if you startup your 

affected source before [DATE SIXTY DAYS AFTER PUBLICATION 

OF THE FINAL RULE IN THE FEDERAL REGISTER], you must submit 

an Initial Notification not later than 120 days after [DATE 

SIXTY DAYS AFTER PUBLICATION OF THE FINAL RULE IN THE 

FEDERAL REGISTER].

(c) As specified in §63.9(b)(4) and (b)(5), if you 

startup your new or reconstructed affected source on or 

after [DATE SIXTY DAYS AFTER PUBLICATION OF THE FINAL RULE 
258

IN THE FEDERAL REGISTER], you must submit an Initial 

Notification not later than 15 days after the actual date 

of startup of the affected source.

(d) If you are required to conduct a performance test 

you must submit a Notification of Intent to conduct a 

performance test at least 30 days before the performance 

test is scheduled to begin.

(e) If you are required to conduct an initial 

compliance demonstration as specified in §63.7530(a), you 

must submit a Notification of Compliance Status according 

to §63.9(h)(2)(ii). For each initial compliance 

demonstration, you must submit the Notification of 

Compliance Status, including all performance test results 

and fuel analyses, before the close of business on the 60th 

day following the completion of the performance test and/or 

other initial compliance demonstrations according to 

§63.10(d)(2). The Notification of Compliance Status report 

must contain all the information specified in paragraphs 

(e)(1) through (9), as applicable.

(1) A description of the affected source(s) including 

identification of which subcategory the source is in, the 

design capacity of the source, a description of the add-on 

controls used on the source, description of the fuel(s) 

burned, including whether the fuel(s) were determined by 
259

you or EPA through a petition process to be a non-waste 

under 40 CFR 241.3, whether the fuel(s) were processed from 

discarded non-hazardous secondary materials within the 

meaning of 40 CFR 241.3, and justification for the 

selection of fuel(s) burned during the performance test.

(2) Summary of the results of all performance tests

(stack tests and fuel analyses) and calculations conducted 

to demonstrate initial compliance including all established 

operating limits.

(3) A summary of the CO emissions monitoring data and 

the maximum CO emission levels recorded during the 

performance test to show that you have met any applicable 

emission standard in Table 1 or 2 to this subpart.

(4) Identification of whether you plan to demonstrate 

compliance with each applicable emission limit through 

performance stack testing or fuel analysis.

(5) Identification of whether you plan to demonstrate 

compliance by emissions averaging.

(6) A signed certification that you have met all 

applicable emission limits and work practice standards.

(7) If you had a deviation from any emission limit,

work practice standard, or operating limit, you must also 

submit a description of the deviation, the duration of the 
260

deviation, and the corrective action taken in the 

Notification of Compliance Status report.

(f) If you operate a natural gas-fired boiler or 

process heater that is subject to this subpart, and you 

intend to use a fuel other than natural gas or equivalent 

to fire the affected unit, you must submit a notification 

of alternative fuel use within 48 hours of the declaration 

of a period of natural gas curtailment or supply 

interruption, as defined in §63.7575. The notification must 

include the information specified in paragraphs (f)(1) 

through (5) of this section.

(1) Company name and address.

(2) Identification of the affected unit.

(3) Reason you are unable to use natural gas or 

equivalent fuel, including the date when the natural gas 

curtailment was declared or the natural gas supply 

interruption began.

(4) Type of alternative fuel that you intend to use.

(5) Dates when the alternative fuel use is expected to 

begin and end.

§ 63.7550 What reports must I submit and when?

(a) You must submit each report in Table 9 to this 

subpart that applies to you.
261

(b) Unless the EPA Administrator has approved a 

different schedule for submission of reports under 

§63.10(a), you must submit each report by the date in Table 

9 to this subpart and according to the requirements in 

paragraphs (b)(1) through (5) of this section.

(1) The first compliance report must cover the period 

beginning on the compliance date that is specified for your 

affected source in §63.7495 and ending on June 30 or 

December 31, whichever date is the first date that occurs 

at least 180 days after the compliance date that is 

specified for your source in §63.7495.

(2) The first compliance report must be postmarked or 

delivered no later than July 31 or January 31, whichever 

date is the first date following the end of the first 

calendar half after the compliance date that is specified 

for your source in §63.7495.

(3) Each subsequent compliance report must cover the 

semiannual reporting period from January 1 through June 30 

or the semiannual reporting period from July 1 through 

December 31.

(4) Each subsequent compliance report must be 

postmarked or delivered no later than July 31 or January 

31, whichever date is the first date following the end of 

the semiannual reporting period.
262

(5) For each affected source that is subject to 

permitting regulations pursuant to 40 CFR part 70 or 40 CFR 

part 71, and if the permitting authority has established 

dates for submitting semiannual reports pursuant to 40 CFR 

70.6(a)(3)(iii)(A) or 40 CFR 71.6(a)(3)(iii)(A), you may 

submit the first and subsequent compliance reports 

according to the dates the permitting authority has 

established instead of according to the dates in paragraphs 

(b)(1) through (4) of this section.

(c) The compliance report must contain the information 

required in paragraphs (c)(1) through (11) of this section.

(1) Company name and address.

(2) Statement by a responsible official with that 

official's name, title, and signature, certifying the 

truth, accuracy, and completeness of the content of the 

report.

(3) Date of report and beginning and ending dates of 

the reporting period.

(4) The total fuel use by each affected source subject 

to an emission limit, for each calendar month within the 

semiannual reporting period, including, but not limited to, 

a description of the fuel, whether the fuel has received a 

non-waste determination by EPA or your basis for concluding 
263

that the fuel is not a waste, and the total fuel usage 

amount with units of measure.

(5) A summary of the results of the annual performance 

tests and documentation of any operating limits that were 

reestablished during this test, if applicable. If you are 

conducting stack tests once every three years consistent 

with section 63.7515(b) or (c), the date of the last three 

stack tests, a comparison of the emission level you 

achieved in the last three stack tests to the 90 percent

emission limit threshold required in section 63.7515(b) or 

(c), and a statement as to whether there have been any 

operational changes since the last stack test that could 

increase emissions.

(6) A signed statement indicating that you burned no 

new types of fuel. Or, if you did burn a new type of fuel, 

you must submit the calculation of chlorine input, using 

Equation 5 of §63.7530, that demonstrates that your source 

is still within its maximum chlorine input level 

established during the previous performance testing (for 

sources that demonstrate compliance through performance 

testing) or you must submit the calculation of HCl emission 

rate using Equation 9 of §63.7530 that demonstrates that 

your source is still meeting the emission limit for HCl 

emissions (for boilers or process heaters that demonstrate 
264

compliance through fuel analysis). If you burned a new 

type of fuel, you must submit the calculation of mercury 

input, using Equation 7 of §63.7530, that demonstrates that 

your source is still within its maximum mercury input level 

established during the previous performance testing (for 

sources that demonstrate compliance through performance 

testing), or you must submit the calculation of mercury 

emission rate using Equation 11 of §63.7530 that 

demonstrates that your source is still meeting the emission 

limit for mercury emissions (for boilers or process heaters 

that demonstrate compliance through fuel analysis).

(7) If you wish to burn a new type of fuel and you can 

not demonstrate compliance with the maximum chlorine input 

operating limit using Equation 5 of §63.7530 or the maximum 

mercury input operating limit using Equation 7 of §63.7530, 

you must include in the compliance report a statement 

indicating the intent to conduct a new performance test 

within 60 days of starting to burn the new fuel.

(8) The hours of operation for each boiler and process 

heater that is subject to an emission limit for each 

calendar month within the semiannual reporting period. This 

requirement applies only to limited use boilers and process 

heaters.
265

(9) If there are no deviations from any emission 

limits or operating limits in this subpart that apply to 

you, a statement that there were no deviations from the 

emission limits or operating limits during the reporting 

period.

(10) If there were no deviations from the monitoring 

requirements including no periods during which the CMSs, 

including CEMS, COMS, and CPMS, were out of control as 

specified in §63.8(c)(7), a statement that there were no 

deviations and no periods during which the CMS were out of 

control during the reporting period.

(d) For each deviation from an emission limit or 

operating limit in this subpart that occurs at an affected 

source where you are not using a CMS to comply with that 

emission limit or operating limit, the compliance report 

must additionally contain the information required in 

paragraphs (d)(1) through (4) of this section.

(1) The total operating time of each affected source 

during the reporting period.

(2) A description of the deviation and which emission 

limit or operating limit from which you deviated.

(3) Information on the number, duration, and cause of 

deviations (including unknown cause), as applicable, and 

the corrective action taken.
266

(4) A copy of the test report if the annual 

performance test showed a deviation from the emission 

limits.

(e) For each deviation from an emission limit, 

operating limit, and monitoring requirement in this subpart 

occurring at an affected source where you are using a CMS 

to comply with that emission limit or operating limit, you 

must include the information required in paragraphs (e) (1) 

through (12) of this section. This includes any deviations 

from your site-specific monitoring plan as required in 

§63.7505(d).

(1) The date and time that each deviation started and 

stopped and description of the nature of the deviation 

(i.e., what you deviated from).

(2) The date and time that each CMS was inoperative, 

except for zero (low-level) and high-level checks.

(3) The date, time, and duration that each CMS was out 

of control, including the information in §63.8(c)(8).

(4) The date and time that each deviation started and 

stopped, and whether each deviation occurred during a 

period of startup, shutdown, or malfunction or during 

another period.

(5) A summary of the total duration of the deviation 

during the reporting period and the total duration as a 
267

percent of the total source operating time during that 

reporting period.

(6) An analysis of the total duration of the 

deviations during the reporting period into those that are 

due to startup, shutdown, control equipment problems, 

process problems, other known causes, and other unknown 

causes.

(7) A summary of the total duration of CMSs downtime 

during the reporting period and the total duration of CMS 

downtime as a percent of the total source operating time 

during that reporting period.

(8) An identification of each parameter that was 

monitored at the affected source for which there was a 

deviation.

(9) A brief description of the source for which there 

was a deviation.

(10) A brief description of each CMS for which there 

was a deviation.

(11) The date of the latest CMS certification or audit 

for the system for which there was a deviation.

(12) A description of any changes in CMSs, processes, 

or controls since the last reporting period for the source 

for which there was a deviation.
268

(f) Each affected source that has obtained a title V 

operating permit pursuant to 40 CFR part 70 or 40 CFR part 

71 must report all deviations as defined in this subpart in 

the semiannual monitoring report required by 40 CFR 

70.6(a)(3)(iii)(A) or 40 CFR 71.6(a)(3)(iii)(A). If an 

affected source submits a compliance report pursuant to 

Table 9 to this subpart along with, or as part of, the 

semiannual monitoring report required by 40 CFR 

70.6(a)(3)(iii)(A) or 40 CFR 71.6(a)(3)(iii)(A), and the 

compliance report includes all required information 

concerning deviations from any emission limit, operating 

limit, or work practice requirement in this subpart, 

submission of the compliance report satisfies any 

obligation to report the same deviations in the semiannual 

monitoring report. However, submission of a compliance 

report does not otherwise affect any obligation the 

affected source may have to report deviations from permit 

requirements to the permit authority.

(g) In addition to the information required in 

§63.9(h)(2), your notification must include the following 

certification(s) of compliance, as applicable, and signed 

by a responsible official:

(i) “This facility complies with the requirements in 

§63.7540(a)(10) to conduct an annual tune-up of the unit”.
269

(ii) “This facility has had an energy assessment 

performed according to §63.7530(e).”

(iii) “No secondary materials that are solid waste 

were combusted in any affected unit.”

(h) After December 31, 2011, within 60 days after the date 

of completing each performance evaluation conducted to 

demonstrate compliance with this subpart, the owner or 

operator of the affected facility must submit the test data 

to EPA by entering the data electronically into EPA’s

WebFIRE data base through EPA’s Central Data Exchange. The 

owner or operator of an affected facility shall enter the 

test data into EPA’s data base using the Electronic 

Reporting Tool or other compatible electronic spreadsheet. 

Only performance evaluation data collected using methods 

compatible with ERT are subject to this requirement to be 

submitted electronically into EPA’s WebFIRE database. 

§ 63.7555 What records must I keep?

(a) You must keep records according to paragraphs 

(a)(1) through (3) of this section.

(1) A copy of each notification and report that you 

submitted to comply with this subpart, including all 

documentation supporting any Initial Notification or 

Notification of Compliance Status or semiannual compliance 
270

report that you submitted, according to the requirements in 

§63.10(b)(2)(xiv).

(2) Records of performance stack tests, fuel analyses, 

or other compliance demonstrations, performance 

evaluations, and opacity observations as required in 

§63.10(b)(2)(viii).

(b) For each CEMS, CPMS, and COMS, you must keep 

records according to paragraphs (b)(1) through (5) of this 

section.

(1) Records described in §63.10(b)(2) (vi) through 

(xi).

(2) Monitoring data for continuous opacity monitoring 

system during a performance evaluation as required in 

§63.6(h)(7)(i) and (ii).

(3) Previous ( i.e., superseded) versions of the 

performance evaluation plan as required in §63.8(d)(3).

(4) Request for alternatives to relative accuracy test 

for CEMS as required in §63.8(f)(6)(i).

(5) Records of the date and time that each deviation 

started and stopped, and whether the deviation occurred 

during a period of startup, shutdown, or malfunction or 

during another period.

(c) You must keep the records required in Table 8 to 

this subpart including records of all monitoring data and 
271

calculated averages for applicable operating limits such as 

opacity, pressure drop, and pH to show continuous 

compliance with each emission limit and operating limit

that applies to you.

(d) For each boiler or process heater subject to an 

emission limit, you must also keep the records in 

paragraphs (d)(1) through (5) of this section.

(1) You must keep records of monthly fuel use by each 

boiler or process heater, including the type(s) of fuel and 

amount(s) used.

(2) If you combust non-hazardous secondary materials 

that have been determined not to be solid waste pursuant to 

40 CFR 41.3(b)(1), you must keep a record which documents 

how the secondary material meets each of the legitimacy 

criteria. If you combust a fuel that has been processed 

from a discarded non-hazardous secondary material pursuant 

to 241.3(b)(2), you must keep records as to how the 

operations that produced the fuel satisfies the definition 

of processing in 40 CFR 241.2. If the fuel received a nonwaste determination pursuant to the petition process 

submitted under 40 CFR 241.3(c), you must keep a record 

which documents how the fuel satisfies the requirements of 

the petition process.
272

(3) You must keep records of monthly hours of 

operation by each boiler or process heater. This 

requirement applies only to limited-use boilers and process 

heaters.

(4) A copy of all calculations and supporting 

documentation of maximum chlorine fuel input, using 

Equation 5 of §63.7530, that were done to demonstrate 

continuous compliance with the HCl emission limit, for 

sources that demonstrate compliance through performance 

testing. For sources that demonstrate compliance through 

fuel analysis, a copy of all calculations and supporting 

documentation of HCl emission rates, using Equation 9 of 

§63.7530, that were done to demonstrate compliance with the 

HCl emission limit. Supporting documentation should include 

results of any fuel analyses and basis for the estimates of 

maximum chlorine fuel input or HCl emission rates. You can 

use the results from one fuel analysis for multiple boilers 

and process heaters provided they are all burning the same 

fuel type. However, you must calculate chlorine fuel input, 

or HCl emission rate, for each boiler and process heater.

(5) A copy of all calculations and supporting 

documentation of maximum mercury fuel input, using Equation 

7 of §63.7530, that were done to demonstrate continuous 

compliance with the mercury emission limit for sources that 
273

demonstrate compliance through performance testing. For 

sources that demonstrate compliance through fuel analysis, 

a copy of all calculations and supporting documentation of 

mercury emission rates, using Equation 11 of §63.7530, that 

were done to demonstrate compliance with the mercury 

emission limit. Supporting documentation should include 

results of any fuel analyses and basis for the estimates of 

maximum mercury fuel input or mercury emission rates. You 

can use the results from one fuel analysis for multiple 

boilers and process heaters provided they are all burning 

the same fuel type. However, you must calculate mercury 

fuel input, or mercury emission rates, for each boiler and 

process heater.

(6) If consistent with 63.7555(b) and (c), you choose 

to stack test less frequently than annually, you must keep 

annual records that document that your emissions in the 

previous stack test(s) were less than 90 percent of the 

applicable emission limit, and document that there was no 

change in source operations including fuel composition and 

operation of air pollution control equipment that would 

cause emissions of the relevant pollutant to increase 

within the past year.

(7) If you operate a gaseous fuel unit that is subject 

to the emission limits specified in Table 1 or 2 to this 
274

subpart, and you intend to use a fuel other than natural 

gas or equivalent to fire the affected unit, you must keep 

records of the information required by the notification 

under 63.XXXX, and records of the total hours per calendar 

year that liquid fuel is burned.

(e) If you elect to average emissions consistent with 

63.7522, you must additionally keep a copy of the emission 

averaging implementation plan required in 63.7522(g), all 

calculations required under 63.7522, including daily 

records of heat input or steam generation, as applicable, 

and monitoring records consistent with 63.7541. 

§ 63.7560 In what form and how long must I keep my 

records?

(a) Your records must be in a form suitable and 

readily available for expeditious review, according to 

§63.10(b)(1).

(b) As specified in §63.10(b)(1), you must keep each 

record for 5 years following the date of each occurrence, 

measurement, maintenance, corrective action, report, or 

record.

(c) You must keep each record on site for at least 2 

years after the date of each occurrence, measurement, 

maintenance, corrective action, report, or record, 
275

according to §63.10(b)(1). You can keep the records off 

site for the remaining 3 years.

OTHER REQUIREMENTS AND INFORMATION

§ 63.7565 What parts of the General Provisions apply to 

me?

Table 10 to this subpart shows which parts of the 

General Provisions in §§63.1 through 63.15 apply to you.

§ 63.7570 Who implements and enforces this subpart?

(a) This subpart can be implemented and enforced by 

U.S. EPA, or a delegated authority such as your State, 

local, or tribal agency. If the EPA Administrator has 

delegated authority to your State, local, or tribal agency, 

then that agency (as well as the U.S. EPA) has the 

authority to implement and enforce this subpart. You 

should contact your EPA Regional Office to find out if this 

subpart is delegated to your State, local, or tribal 

agency.

(b) In delegating implementation and enforcement 

authority of this subpart to a State, local, or tribal 

agency under 40 CFR part 63, subpart E, the authorities 

listed in paragraphs (b)(1) through (5) of this section are 

retained by the EPA Administrator and are not transferred 

to the State, local, or tribal agency, however, the U.S. 
276

EPA retains oversight of this subpart and can take 

enforcement actions, as appropriate.

(1) Approval of alternatives to the non-opacity 

emission limits and work practice standards in §63.7500(a) 

and (b) under §63.6(g).

(2) Approval of alternative opacity emission limits in 

§63.7500(a) under §63.6(h)(9).

(3) Approval of major change to test methods in Table 

5 to this subpart under §63.7(e)(2)(ii) and (f) and as 

defined in §63.90, and alternative analytical methods 

requested under 63.7521(b)(2).

(4) Approval of major change to monitoring under 

§63.8(f) and as defined in §63.90, and approval of 

alternative operating parameters under 63.7500(a)(2) and 

63.7522(g)(2).

(5) Approval of major change to recordkeeping and 

reporting under §63.10(e) and as defined in §63.90.

§ 63.7575 What definitions apply to this subpart?

Terms used in this subpart are defined in the CAA, in

§63.2 (the General Provisions), and in this section as 

follows:

Bag leak detection system means a group of instruments

that are capable of monitoring particulate matter loadings 

in the exhaust of a fabric filter (i.e., baghouse) in order 
277

to detect bag failures. A bag leak detection system 

includes, but is not limited to, an instrument that 

operates on electrodynamic, triboelectric, light 

scattering, light transmittance, or other principle to 

monitor relative particulate matter loadings.

Biomass fuel means but is not limited to, wood 

residue, and wood products (e.g., trees, tree stumps, tree 

limbs, bark, lumber, sawdust, sanderdust, chips, scraps, 

slabs, millings, and shavings); animal manure, including 

litter other bedding materials; vegetative agricultural and 

silvicultural materials, such as logging residues (slash), 

nut and grain hulls and chaff (e.g., almond, walnut, 

peanut, rice, and wheat), bagasse, orchard prunings, corn 

stalks, coffee bean hulls and grounds. This definition of 

biomass fuel is not intended to suggest that these 

materials are or not solid waste.

Blast furnace gas fuel-fired boiler or process heater

means an industrial/commercial/institutional boiler or 

process heater that receives 90 percent or more of its 

total heat input (based on an annual average) from blast 

furnace gas.

Boiler means an enclosed device using controlled flame 

combustion and having the primary purpose of recovering 

thermal energy in the form of steam or hot water. A device 
278

combusting solid waste, as defined in 40 CFR 241.3, is not 

a boiler. Waste heat boilers are excluded from this 

definition.

Coal means all solid fuels classifiable as anthracite, 

bituminous, sub-bituminous, or lignite by the American 

Society for Testing and Materials in ASTM D388–991.1 , 

“Standard Specification for Classification of Coals by Rank1

” (incorporated by reference, see §63.14(b)), coal refuse, 

and petroleum coke. Synthetic fuels derived from coal for 

the purpose of creating useful heat including but not 

limited to, solvent-refined coal, coal-oil mixtures, and 

coal-water mixtures, for the purposes of this subpart. 

Coal derived gases are excluded from this definition.

Coal refuse means any by-product of coal mining or 

coal cleaning operations with an ash content greater than 

50 percent (by weight) and a heating value less than 13,900 

kilojoules per kilogram (6,000 Btu per pound) on a dry 

basis.

Commercial/institutional boiler means a boiler used in 

commercial establishments or institutional establishments 

such as medical centers, research centers, institutions of 

higher education, hotels, and laundries to provide 

electricity, steam, and/or hot water.
279

Common Stack means the exhaust of emissions from two 

or more affected units through a single flue.

Cost-effective energy conservation measure means a 

measure that is implemented to improve the energy 

efficiency of the boiler or facility that has a payback 

(return of investment) period of three or fewer years. 

Deviation. (1) Deviation means any instance in which 

an affected source subject to this subpart, or an owner or 

operator of such a source:

(i) Fails to meet any requirement or obligation 

established by this subpart including, but not limited to, 

any emission limit, operating limit, or work practice 

standard; or

(ii) Fails to meet any term or condition that is 

adopted to implement an applicable requirement in this 

subpart and that is included in the operating permit for 

any affected source required to obtain such a permit.

(2) A deviation is not always a violation. The 

determination of whether a deviation constitutes a 

violation of the standard is up to the discretion of the 

entity responsible for enforcement of the standards.

Distillate oil means fuel oils, including recycled 

oils, that comply with the specifications for fuel oil 

numbers 1 and 2, as defined by the American Society for 
280

Testing and Materials in ASTM D396–02a, “Standard 

Specifications for Fuel Oils1 ” (incorporated by reference, 

see §63.14(b)).

Dry scrubber means an add-on air pollution control 

system that injects dry alkaline sorbent (dry injection) or 

sprays an alkaline sorbent (spray dryer) to react with and 

neutralize acid gas in the exhaust stream forming a dry 

powder material. Sorbent injection systems in fluidized 

bed boilers and process heaters are included in this 

definition.

Dutch oven means a unit having a refractory-walled 

cell connected to a conventional boiler setting. Fuel

materials are introduced through an opening in the roof of 

the Dutch oven and burn in a pile on its floor.

Electric utility steam generating unit means a fossil 

fuel-fired combustion unit of more than 25 megawatts that 

serves a generator that produces electricity for sale. A 

fossil fuel-fired unit that cogenerates steam and 

electricity and supplies more than one-third of its 

potential electric output capacity and more than 25 

megawatts electrical output to any utility power 

distribution system for sale is considered an electric 

utility steam generating unit.
281

Electrostatic precipitator means an add-on air 

pollution control device used to capture particulate matter 

by charging the particles using an electrostatic field, 

collecting the particles using a grounded collecting 

surface, and transporting the particles into a hopper.

Energy assessment means an in-depth assessment of a 

facility to identify immediate and long-term opportunities 

to save energy, focusing on the steam and process heating 

systems which involves a thorough examination of potential 

savings from energy efficiency improvements, waste 

minimization and pollution prevention, and productivity 

improvement.

Equivalent means the following only as this term is 

used in Table 6 to subpart DDDDD:

(1) An equivalent sample collection procedure means a 

published voluntary consensus standard or practice (VCS) or 

EPA method that includes collection of a minimum of three 

composite fuel samples, with each composite consisting of a 

minimum of three increments collected at approximately 

equal intervals over the test period.

(2) An equivalent sample compositing procedure means a 

published VCS or EPA method to systematically mix and 

obtain a representative subsample (part) of the composite 

sample.
282

(3) An equivalent sample preparation procedure means a 

published VCS or EPA method that: Clearly states that the 

standard, practice or method is appropriate for the 

pollutant and the fuel matrix; or is cited as an 

appropriate sample preparation standard, practice or method 

for the pollutant in the chosen VCS or EPA determinative or 

analytical method.

(4) An equivalent procedure for determining heat 

content means a published VCS or EPA method to obtain gross 

calorific (or higher heating) value.

(5) An equivalent procedure for determining fuel 

moisture content means a published VCS or EPA method to 

obtain moisture content. If the sample analysis plan calls 

for determining metals (especially the mercury, selenium, 

or arsenic) using an aliquot of the dried sample, then the 

drying temperature must be modified to prevent vaporizing 

these metals. On the other hand, if metals analysis is done 

on an “as received” basis, a separate aliquot can be dried 

to determine moisture content and the metals concentration 

mathematically adjusted to a dry basis.

(6) An equivalent pollutant (mercury) determinative or 

analytical procedure means a published VCS or EPA method 

that clearly states that the standard, practice, or method 

is appropriate for the pollutant and the fuel matrix and 
283

has a published detection limit equal or lower than the 

methods listed in Table 6 to subpart DDDDD for the same 

purpose.

Fabric filter means an add-on air pollution control 

device used to capture particulate matter by filtering gas 

streams through filter media, also known as a baghouse.

Federally enforceable means all limitations and 

conditions that are enforceable by the EPA Administrator, 

including the requirements of 40 CFR parts 60 and 61, 

requirements within any applicable State implementation 

plan, and any permit requirements established under 40 CFR 

52.21 or under 40 CFR 51.18 and 40 CFR 51.24.

Fuel type means each category of fuels that share a 

common name or classification. Examples include, but are 

not limited to, bituminous coal, subbituminous coal, 

lignite, anthracite, biomass, residual oil. Individual 

fuel types received from different suppliers are not 

considered new fuel types. 

Fluidized Bed Boiler means a boiler utilizing a 

fluidized bed combustion process. 

Fluidized bed combustion means a process where a fuel 

is burned in a bed of granulated particles which are 

maintained in a mobile suspension by the forward flow of 

air and combustion products.
284

Fuel cell means a boiler type in which the fuel is 

dropped onto suspended fixed grates and is fired in a pile. 

The refractory-lined fuel cell uses combustion air 

preheating and positioning of secondary and tertiary air 

injection ports to improve boiler efficiency.

Gaseous fuel includes, but is not limited to, natural 

gas, process gas, landfill gas, coal derived gas, refinery 

gas, and biogas. Blast furnace gas is exempted from this 

definition.

Heat input means heat derived from combustion of fuel 

in a boiler or process heater and does not include the heat 

input from preheated combustion air, recirculated flue 

gases, or exhaust gases from other sources such as gas 

turbines, internal combustion engines, kilns, etc.

Hot water heater means a closed vessel with a capacity 

of no more than 120 U.S. gallons in which water is heated 

by combustion of gaseous or liquid fuel and is withdrawn 

for use external to the vessel at pressures not exceeding 

160 psig, including the apparatus by which the heat is 

generated and all controls and devices necessary to prevent 

water temperatures from exceeding 210 °F (99 °C).

Industrial boiler means a boiler used in 

manufacturing, processing, mining, and refining or any 
285

other industry to provide steam, hot water, and/or 

electricity.

Liquid fuel subcategory includes any boiler or process 

heater of any design that does not burn any solid fuel and 

burns any liquid fuel either alone or in combination with 

gaseous fuels. Gaseous fuel boilers and process heaters 

that burn liquid fuel during periods of gas curtailment, 

gas supply emergencies or for periodic testing of liquid 

fuel not to exceed a combined total of 48 hours during any 

calendar year are not included in this definition.

Liquid fuel includes, but is not limited to, 

distillate oil, residual oil, on-spec used oil, and process 

liquids.

Metal process furnaces include natural gas-fired

annealing furnaces, preheat furnaces, reheat furnaces, 

aging furnaces, and heat treat furnaces.

Minimum pressure drop means 90 percent of the test 

average pressure drop measured according to Table 7 to this 

subpart during the most recent performance test 

demonstrating compliance with the applicable emission 

limit.

Minimum scrubber effluent pH means 90 percent of the 

test average effluent pH measured at the outlet of the wet 

scrubber according to Table 7 to this subpart during the 
286

most recent performance test demonstrating compliance with 

the applicable hydrogen chloride emission limit.

Minimum scrubber flow rate means 90 percent of the 

test average flow rate measured according to Table 7 to 

this subpart during the most recent performance test 

demonstrating compliance with the applicable emission 

limit.

Minimum sorbent flow rate means 90 percent of the test 

average sorbent (or activated carbon) flow rate measured 

according to Table 7 to this subpart during the most recent 

performance test demonstrating compliance with the 

applicable emission limits.

Minimum voltage or amperage means 90 percent of the 

test average voltage or amperage to the electrostatic 

precipitator measured according to Table 7 to this subpart 

during the most recent performance test demonstrating 

compliance with the applicable emission limits.

Natural gas means:

(1) A naturally occurring mixture of hydrocarbon and 

nonhydrocarbon gases found in geologic formations beneath 

the earth's surface, of which the principal constituent is 

methane; or

(2) Liquid petroleum gas, as defined by the American 

Society for Testing and Materials in ASTM D1835–03a, 
287

“Standard Specification for Liquid Petroleum Gases” 

(incorporated by reference, see §63.14(b)).

Opacity means the degree to which emissions reduce the 

transmission of light and obscure the view of an object in 

the background.

Particulate matter means any finely divided solid or 

liquid material, other than uncombined water, as measured 

by the test methods specified under this subpart, or an 

alternative method.

Period of natural gas curtailment or supply 

interruption means a period of time during which the supply 

of natural gas to an affected facility is halted for 

reasons beyond the control of the facility. An increase in 

the cost or unit price of natural gas does not constitute a 

period of natural gas curtailment or supply interruption.

Process heater means an enclosed device using 

controlled flame, that is not a boiler, and the unit's 

primary purpose is to transfer heat indirectly to a process 

material (liquid, gas, or solid) or to a heat transfer 

material for use in a process unit, instead of generating 

steam. Process heaters are devices in which the combustion 

gases do not directly come into contact with process 

materials. A device combusting solid waste, as defined in 

40 CFR 241.3, is not a process heater. Process heaters do 
288

not include units used for comfort heat or space heat, food 

preparation for on-site consumption, or autoclaves.

Pulverized coal boiler means a boiler in which 

pulverized coal is introduced into an air stream that 

carries the coal to the combustion chamber of the boiler 

where it is fired in suspension.

Qualified personnel mean specialists in evaluating 

energy systems who have successfully completed the DOE 

Qualified Specialist program or the equivalent.

Residual oil means crude oil, and all fuel oil numbers 

4, 5 and 6, as defined by the American Society for Testing 

and Materials in ASTM D396–02a, “Standard Specifications 

for Fuel Oils1 ” (incorporated by reference, see §63.14(b)).

Responsible official means responsible official as 

defined in 40 CFR 70.2.

Stoker means a unit consisting of a mechanically 

operated fuel feeding mechanism, a stationary or moving 

grate to support the burning of fuel and admit undergrate 

air to the fuel, an overfire air system to complete 

combustion, and an ash discharge system. There are two 

general types of stokers: underfeed and overfeed. Overfeed 

stokers include mass feed and spreader stokers.

Suspension boiler means a unit designed to feed the 

fuel by means of fuel distributors. The distributors 
289

inject air at the point where the fuel is introduced into 

the boiler in order to spread the fuel material over the 

boiler width. The drying (and much of the combustion) 

occurs while the material is suspended in air. The 

combustion of the fuel material is completed on a grate or 

floor below. Suspension boilers almost universally are 

designed to have high heat release rates to quickly dry the 

wet fuel as it is blown into the boilers.

Temporary boiler means any gaseous or liquid fuel

boiler that is designed to, and is capable of, being 

carried or moved from one location to another. A temporary 

boiler that remains at a location for more than 180 

consecutive days is no longer considered to be a temporary 

boiler. Any temporary boiler that replaces a temporary 

boiler at a location and is intended to perform the same or 

similar function will be included in calculating the 

consecutive time period.

Tune-up means adjustments made to a boiler in 

accordance with procedures supplied by the manufacturer (or 

an approved specialist) to optimize the combustion 

efficiency.

Unit designed to burn biomass subcategory includes any 

boiler or process heater that burns at least 10 percent

biomass, but less than 10 percent coal, on a heat input 
290

basis on an annual average, either alone or in combination 

with liquid fuels or gaseous fuels.

Unit designed to burn coal subcategory includes any 

boiler or process heater that burns at least 10 percent

coal on a heat input basis on an annual average either 

alone or in combination with biomass, liquid fuels, or 

gaseous fuels.

Unit designed to burn gas 1 (NG/RG) subcategory

includes any boiler or process heater that burns at least 

90 percent natural gas and/or refinery gas on a heat input 

basis on an annual average.

Unit designed to burn gas 2 (other) subcategory

includes any boiler or process heater that burns gaseous 

fuels other than natural gas and/or refinery gas not 

combined with any solid or liquid fuels.

Unit designed to burn oil subcategory includes any 

boiler or process heater that burns any liquid fuel, but 

less than 10 percent solid fuel on a heat input basis on an 

annual average, either alone or in combination with gaseous 

fuels. Gaseous fuel boilers and process heaters that burn 

liquid fuel during periods of gas curtailment, gas supply 

emergencies or for periodic testing of liquid fuel not to 

exceed a combined total of 48 hours during any calendar 

year are not included in this definition.
291

Voluntary Consensus Standards or VCS mean technical 

standards ( e.g. , materials specifications, test methods, 

sampling procedures, business practices) developed or 

adopted by one or more voluntary consensus bodies. 

EPA/OAQPS has by precedent only used VCS that are written 

in English. Examples of VCS bodies are: American Society of 

Testing and Materials (ASTM), American Society of 

Mechanical Engineers (ASME), International Standards 

Organization (ISO), Standards Australia (AS), British 

Standards (BS), Canadian Standards (CSA), European Standard 

(EN or CEN) and German Engineering Standards (VDI). The 

types of standards that are not considered VCS are 

standards developed by: the U.S. states, e.g. , California 

(CARB) and Texas (TCEQ); industry groups, such as American 

Petroleum Institute (API), Gas Processors Association 

(GPA), and Gas Research Institute (GRI); and other branches 

of the U.S. government, e.g. Department of Defense (DOD) 

and Department of Transportation (DOT). This does not 

preclude EPA from using standards developed by groups that 

are not VCS bodies within their rule. When this occurs, EPA 

has done searches and reviews for VCS equivalent to these 

non-EPA methods.

Waste heat boiler means a device that recovers 

normally unused energy and converts it to usable heat. 
292

Waste heat recovery boilers incorporating duct or 

supplemental burners that are designed to supply 50 percent 

or more of the total rated heat input capacity of the waste 

heat boiler are not considered waste heat boilers, but are 

considered boilers. Waste heat boilers are also referred 

to as heat recovery steam generators.

Waste heat process heater

Wet scrubber means any add-on air pollution control 

device that mixes an aqueous stream or slurry with the 

exhaust gases from a boiler or process heater to control 

emissions of particulate matter and/or to absorb and 

neutralize acid gases, such as hydrogen chloride.

means an enclosed device 

that recovers normally unused energy and converts it to 

usable heat. Waste heat process heaters incorporating duct 

or supplemental burners that are designed to supply 50 

percent or more of the total rated heat input capacity of 

the waste heat process heater are not considered waste heat 

process heaters, but are considered process heaters. Waste 

heat process heaters are also referred to as recuperative 

process heaters.

Work practice standard means any design, equipment, 

work practice, or operational standard, or combination 

thereof, that is promulgated pursuant to section 112(h) of 

the CAA.
293

TABLES TO SUBPART DDDDD OF PART 63

Table 1 to Subpart DDDDD of Part 63—Emission Limits for New 

or Reconstructed Boilers and Process Heaters

As stated in §63.7500, you must comply with the following 

applicable emission limits:

If your boiler or 

process heater is in 

this subcategory ...

For the 

following 

pollutants . . 

.

You must meet the following 

emission limits and work practice 

standards . . .

1. Pulverized coal a. Particulate 

Matter 0.001 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.00006 lb per MMBtu of heat input.

 c. Mercury 2.0E-06 lb per MMBtu of heat input.

 d. CO

90 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.002 ng/dscm (TEQ) corrected to 7 

percent oxygen.

2. Stokers designed 

to burn coal

a. Particulate 

Matter 0.001 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.00006 lb per MMBtu of heat input.

 c. Mercury 2.0E-06 lb per MMBtu of heat input.

 d. CO

7 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr). 

e. Dioxin/Furan 0.003 ng/dscm (TEQ) corrected to 7 

percent oxygen.

3. Fluidized bed 

units designed to 

burn coal

a. Particulate 

Matter 0.001 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.00006 lb per MMBtu of heat input.

 c. Mercury 2.0E-06 lb per MMBtu of heat input.

d. CO

30 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.00003 ng/dscm (TEQ) corrected to 
294

7 percent oxygen.

4. Stokers designed 

to burn biomass

a. Particulate 

Matter 0.008 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.004 lb per MMBtu of heat input.

 c. Mercury 2.0E-07 lb per MMBtu of heat input.

d. CO

560 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.00005 ng/dscm (TEQ) corrected to 

7 percent oxygen.

5. Fluidized bed 

units designed to 

burn biomass

a. Particulate 

Matter 0.008 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.004 lb per MMBtu of heat input.

 c. Mercury 2.0E-07 lb per MMBtu of heat input.

d. CO

40 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.007 ng/dscm (TEQ) corrected to 7 

percent oxygen.

6. Suspension 

burners/Dutch Ovens 

designed to burn 

biomass

a. Particulate 

Matter 0.008 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.004 lb per MMBtu of heat input.

c. Mercury 2.0E-07 lb per MMBtu of heat input.

d. CO

1,010 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.03 ng/dscm (TEQ) corrected to 7 

percent oxygen.

7. Fuel cells 

designed to burn 

biomass

a. Particulate 

Matter 0.008 lb per MMBtu of heat input.

b. Hydrogen 

Chloride 0.004 lb per MMBtu of heat input.

c. Mercury 2.0E-07 lb per MMBtu of heat input.

d. CO

270 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 
295

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.0005 ng/dscm (TEQ) corrected to 7 

percent oxygen.

8. Units designed to 

burn liquid fuel

a. Particulate 

Matter 0.002 lb per MMBtu of heat input.

b. Hydrogen 

Chloride 0.0004 lb per MMBtu of heat input.

c. Mercury 3.0E-07 lb per MMBtu of heat input.

d. CO

1 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.002 ng/dscm (TEQ) corrected to 7 

percent oxygen.

9. Units designed to 

burn other gases

a. Particulate 

Matter 0.003 lb per MMBtu of heat input.

b. Hydrogen 

Chloride 3.0E-06 lb per MMBtu of heat input.

c. Mercury 2.0E-07 lb per MMBtu of heat input.

d. CO

1 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.009 ng/dscm (TEQ) corrected to 7 

percent oxygen.

Table 2 to Subpart DDDDD of Part 63 — Emission Limits for 

Existing Boilers and Process Heaters (Units with heat input 

capacity of 10 million Btu per hour or greater) 

As stated in §63.7500, you must comply with the following 

applicable emission limits:

If your boiler or 

process heater is in 

this subcategory ...

For the 

following 

pollutants . . 

.

You must meet the following 

emission limits and work practice 

standards . . .

1. Pulverized coal a. Particulate 

Matter 0.02 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.008 lb per MMBtu of heat input.

 c. Mercury 3.0E-06 lb per MMBtu of heat input.

 d. CO

90 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 
296

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.004 ng/dscm (TEQ) corrected to 7 

percent oxygen 

2. Stokers designed 

to burn coal

a. Particulate 

Matter 0.02 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.008 lb per MMBtu of heat input.

 c. Mercury 3.0E-06 lb per MMBtu of heat input.

 d. CO

50 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.003 ng/dscm (TEQ) corrected to 7 

percent oxygen

3. Fluidized bed 

units designed to 

burn coal

a. Particulate 

Matter 0.02 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.008 lb per MMBtu of heat input.

 c. Mercury 3.0E-06 lb per MMBtu of heat input.

d. CO

30 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.002 ng/dscm (TEQ) corrected to 7 

percent oxygen

4. Stokers designed 

to burn biomass

a. Particulate 

Matter 0.02 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.006 lb per MMBtu of heat input.

 c. Mercury 9.0E-07 lb per MMBtu of heat input.

d. CO

560 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.004 ng/dscm (TEQ) corrected to 7 

percent oxygen.

5. Fluidized bed 

units designed to 

burn biomass

a. Particulate 

Matter 0.02 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.006 lb per MMBtu of heat input.

 c. Mercury 9.0E-07 lb per MMBtu of heat input.

d. CO

250 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 
297

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.02 ng/dscm (TEQ) corrected to 7 

percent oxygen.

6. Suspension 

burners/Dutch Ovens 

designed to burn 

biomass

a. Particulate 

Matter 0.02 lb per MMBtu of heat input.

 b. Hydrogen 

Chloride 0.006 lb per MMBtu of heat input.

c. Mercury 9.0E-07 lb per MMBtu of heat input.

d. CO

1,010 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.03 ng/dscm (TEQ) corrected to 7 

percent oxygen.

7. Fuel cells 

designed to burn 

biomass

a. Particulate 

Matter 0.02 lb per MMBtu of heat input.

b. Hydrogen 

Chloride 0.006 lb per MMBtu of heat input.

c. Mercury 9.0E-07 lb per MMBtu of heat input.

d. CO

270 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.02 ng/dscm (TEQ) corrected to 7 

percent oxygen.

8. Units designed to 

burn liquid fuel

a. Particulate 

Matter 0.004 lb per MMBtu of heat input.

b. Hydrogen 

Chloride 0.0004 lb per MMBtu of heat input.

c. Mercury 4.0E-06 lb per MMBtu of heat input.

d. CO

1 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.002 ng/dscm (TEQ) corrected to 7 

percent oxygen.

9. Units designed to 

burn other gases

a. Particulate 

Matter 0.05 lb per MMBtu of heat input.

b. Hydrogen 

Chloride 3.0E-06 lb per MMBtu of heat input.

c. Mercury 2.0E-07 lb per MMBtu of heat input.

d. C0 1 ppm by volume on a dry basis 

corrected to 3 percent oxygen (30-
298

day rolling average for units 100 

MMBtu/hr or greater, 3-run average 

for units less than 100 MMBtu/hr).

e. Dioxin/Furan 0.009 ng/dscm (TEQ) corrected to 7 

percent oxygen.

Table 3 to Subpart DDDDD of Part 63 — Work Practice 

Standards

As stated in §§63.11202 and 63.11203, you must comply with 

the following applicable work practice standards:

If your boiler is... You must meet the following...

1. An existing 

boiler or process 

heater with heat 

input capacity of 

less than 10 million 

Btu per hour 

Conduct a tune-up of the boiler 

biennially as specified in 

§63.7540.

2. A new or existing 

boiler or process 

heater in either the 

Gas 1 or Metal 

Process Furnace 

subcategory with

heat input capacity 

of 10 million Btu 

per hour or greater

Conduct a tune-up of the boiler 

annually as specified in 

§63.7540.

3. An existing 

boiler or process 

heaters located at a 

major source

facility

Must have an energy assessment

performed on the major source 

facility by qualified personnel 

which includes: 

(1) a visual inspection of the boiler 

system.

(2) establish operating 

characteristics of the facility, 

energy system specifications, 

operating and maintenance procedures, 

and unusual operating constraints,

(3) identify major energy consuming 

systems,

(4) a review of available 

architectural and engineering plans, 

facility operation and maintenance 

procedures and logs, and fuel usage,

(5) a list of major energy 
299

conservation measures,

(6) the energy savings potential of 

the energy conservation measures 

identified, and

(7) a comprehensive report detailing 

the ways to improve efficiency, the 

cost of specific improvements, 

benefits, and the time frame for 

recouping those investments.

Table 4 to Subpart DDDDD of Part 63 — Operating Limits for 

Boilers and Process Heaters

As stated in §63.7500, you must comply with the applicable 

operating limits:

If you 

demonstrate 

compliance using 

. . . You must meet these operating limits . . .

1. Wet scrubber 

control

a. Maintain the minimum pressure drop and liquid flowrate at or above the operating levels established 

during the performance test according to §63.7530(c) 

and Table 7 to this subpart.

2. Fabric filter 

control

a. Install and operate a bag leak detection system 

according to §63.7525 and operate the fabric filter 

such that the bag leak detection system alarm does not 

sound more than 5 percent of the operating time during 

each 6-month period; or

 b. This option is for boilers and process heaters that 

operate dry control systems. Existing and new boilers 

and process heaters must maintain opacity to less than 

or equal to 10 percent (daily block average).

3. Electrostatic 

precipitator 

control

a. This option is for boilers and process heaters that 

operate dry control systems. Existing and new boilers 

and process heaters must maintain opacity to less than 

or equal to 10 percent opacity (daily block average); 

or

 b. This option is only for boilers and process heaters 

that operate additional wet control systems. Maintain 

the minimum voltage and secondary current or total 

power input of the electrostatic precipitator at or 

above the operating limits established during the 

performance test according to §63.7530(c) and Table 7 

to this subpart.

4. Dry scrubber 

or carbon 

injection control

Maintain the minimum sorbent or carbon injection rate 

at or above the operating levels established during 

the performance test according to §63.7530(c) and 

Table 7 to this subpart.
300

5. Any other 

control type

This option is for boilers and process heaters that 

operate dry control systems. Existing and new boilers 

and process heaters must maintain opacity to less than

or equal to 10 percent opacity (daily block average).

6. Fuel analysis Maintain the fuel type or fuel mixture such that the 

applicable emission rates calculated according to 

§63.7530(d)(3),(4) and/or(5) is less than the 

applicable emission limits.

Table 5 to Subpart DDDDD of Part 63—Performance Testing 

Requirements

As stated in §63.7520, you must comply with the following 

requirements for performance test for existing, new or 

reconstructed affected sources:

To conduct a 

performance test 

for the following

pollutant . . . You must . . . Using . . .

1. Particulate 

Matter

a. Select sampling 

ports location and 

the number of 

traverse points

Method 1 in appendix A to part 

60 of this chapter.

 b. Determine velocity 

and volumetric flowrate of the stack gas

Method 2, 2F, or 2G in 

appendix A to part 60 of this 

chapter.

 c. Determine oxygen 

and carbon dioxide 

concentrations of the 

stack gas

Method 3A or 3B in appendix A 

to part 60 of this chapter, or 

ASME PTC 19, Part 10 (1981) 

(IBR, see §63.14(i)).

 d. Measure the 

moisture content of 

the stack gas

Method 4 in appendix A to part 

60 of this chapter.

 e. Measure the 

particulate matter 

emission 

concentration

Method 5 or 17 (positive 

pressure fabric filters must 

use Method 5D) in appendix A 

to part 60 of this chapter.

 f. Convert emissions 

concentration to lb 

per MMBtu emission 

rates

Method 19 F-factor methodology 

in appendix A to part 60 of 

this chapter.

2. Hydrogen 

chloride

a. Select sampling 

ports location and 

the number of 

traverse points

Method 1 in appendix A to part 

60 of this chapter.
301

 b. Determine velocity 

and volumetric flowrate of the stack gas

Method 2, 2F, or 2G in 

appendix A to part 60 of this 

chapter.

 c. Determine oxygen 

and carbon dioxide 

concentrations of the 

stack gas

Method 3A or 3B in appendix A 

to part 60 of this chapter, or 

ASME PTC 19, Part 10 (1981) 

(IBR, see §63.14(i)).

 d. Measure the 

moisture content of 

the stack gas

Method 4 in appendix A to part 

60 of this chapter.

 e. Measure the 

hydrogen chloride 

emission 

concentration

Method 26 or 26A in appendix A 

to part 60 of this chapter.

 f. Convert emissions 

concentration to lb 

per MMBtu emission 

rates

Method 19 F-factor methodology 

in appendix A to part 60 of 

this chapter.

3. Mercury a. Select sampling 

ports location and 

the number of 

traverse points

Method 1 in appendix A to part 

60 of this chapter.

 b. Determine velocity 

and volumetric flowrate of the stack gas

Method 2, 2F, or 2G in 

appendix A to part 60 of this 

chapter.

 c. Determine oxygen 

and carbon dioxide 

concentrations of the 

stack gas

Method 3A or 3B in appendix A 

to part 60 of this chapter, or 

ASME PTC 19, Part 10 (1981) 

(IBR, see §62.14(i)).

 d. Measure the 

moisture content of 

the stack gas

Method 4 in appendix A to part 

60 of this chapter.

 e. Measure the 

mercury emission 

concentration

Method 29 in appendix A to 

part 60 of this chapter or 

Method 101A in appendix B to 

part 61 of this chapter or 

ASTM Method D6784–02 (IBR, see 

§63.14(b)).

 f. Convert emissions 

concentration to lb 

per MMBtu emission 

rates

Method 19 F-factor methodology 

in appendix A to part 60 of 

this chapter.

4. CO a. Select the 

sampling ports 

location and the 

number of traverse 

points

Method 1 in appendix A to part 

60 of this chapter.
302

 b. Determine oxygen 

and carbon dioxide 

concentrations of the 

stack gas

Method 3A or 3B in appendix A 

to part 60 of this chapter, or 

ASTM D6522–00 (IBR, see 

§63.14(b)), or ASME PTC 19, 

Part 10 (1981) (IBR, see 

§63.14(i)).

 c. Measure the 

moisture content of 

the stack gas

Method 4 in appendix A to part 

60 of this chapter.

 d. Measure the CO

emission 

concentration

Method 10 in appendix A to 

part 60 of this chapter.

5. Dioxin/Furan a. Select the 

sampling ports 

location and the 

number of traverse 

points

Method 1 in appendix A to part 

60 of this chapter.

b. Determine oxygen 

and carbon dioxide 

concentrations of the 

stack gas

Method 3A or 3B in appendix A 

to part 60 of this chapter, or 

ASTM D6522–00 (IBR, see 

§63.14(b)), or ASME PTC 19, 

Part 10 (1981) (IBR, see 

§63.14(i)).

c. Measure the 

moisture content of 

the stack gas

Method 4 in appendix A to part 

60 of this chapter.

d. Measure the 

dioxin/furans

emission 

concentration

Method __ in appendix A to 

part 60 of this chapter.

Table 6 to Subpart DDDDD of Part 63—Fuel Analysis 

Requirements

As stated in §63.7521, you must comply with the following 

requirements for fuel analysis testing for existing, new or 

reconstructed affected sources. However, equivalent methods 

may be used in lieu of the prescribed methods at the 

discretion of the source owner or operator:

To conduct 

a fuel

analysis 

for the 

following

pollutant 

* * * You must * * * Using * * *

1. Mercury a. Collect fuel samples Procedure in §63.7521(c) or ASTM 
303

* * * * * * D2234–D2234M–03(for coal) (IBR, see 

§63.14(b)) or ASTM D6323–98 (2003) 

(for biomass) (IBR, See §63.14(b)) 

or equivalent.

 b. Composite fuel 

samples * * *

Procedure in §63.7521(d) or 

equivalent.

 c. Prepare composited 

fuel samples * * *

SW–846–3050B (for solid samples) or 

SW–846–3020A (for liquid samples)

or ASTM D2013–04 (for coal) (IBR, 

see §63.14(b)) or ASTM D5198–92 

(2003) (for biomass) (IBR, see 

§63.14(b)) or equivalent.

 d. Determine heat 

content of the fuel 

type * * *

ASTM D5865–04 (for coal) (IBR, see 

§63.24(b)) or ASTM E711–87 (for 

biomass) (IBR, see §63.14(b)) or 

equivalent.

 e. Determine moisture 

content of the fuel 

type * * *

ASTM D3173–03 (IBR, see §63.14(b)) 

or ASTM E871–82 (1998) (IBR, see 

§63.14(b)) or equivalent.

 f. Measure mercury 

concentration in fuel 

sample * * *

ASTM D6722–01 (for coal) (IBR, see 

§6314(b)) or SW–846–7471A (for 

solid samples) or SW–846–7470A (for 

liquid samples or equivalent.

 g. Convert 

concentration into 

units of pounds of 

pollutant per MMBtu of 

heat content.

2. Hydrogen 

Chloride 

* * *

a. Collect fuel samples 

* * *

Procedure in §63.7521(c) or ASTM 

D2234–D2234M–03(for coal) (IBR, see 

§63.14(b)) or ASTM D6323–98 (2003) 

(for biomass) (IBR, see §63.14(b)) 

or equivalent.

 b. Composite fuel 

samples * * *

Procedure in §63.7521(d) or 

equivalent.

 c. Prepare composited 

fuel samples * * *

SW–846–3050B (for solid samples) or 

SW–846–3020A (for liquid samples) 

or ASTM D2013–04 (for coal) (IBR, 

see §63.14(b)) or ASTM D5198–92 

(2003) (for biomass) (IBR, see 

§63.14(b)) or equivalent.

 d. Determine heat 

content of the fuel 

type * * *

ASTM D5865–04 (for coal) (IBR, see 

§63.14(b)) or ASTM E711–87 (1996) 

(for biomass) (IBR, see §63.14(b)) 

or equivalent.

 e. Determine moisture 

content of the fuel 

type * * *

ASTM D3173–03 (IBR, see §63.14(b)) 

or ASTM E871–82 (1998) or 

equivalent.
304

 f. Measure chlorine 

concentration in fuel 

sample * * *

SW–846–9250 or ASTM D6721–01 (for 

coal) or ASTM E776–87 (1996) (for 

biomass) (IBR, see §63.14(b)) or 

equivalent.

 g. Convert 

concentrations into 

units of pounds of 

pollutant per MMBtu of 

heat content.

[ 71 FR 70663, Dec. 6, 2006]

Table 7 to Subpart DDDDD of Part 63—Establishing Operating 

Limits

As stated in §63.7520, you must comply with the following 

requirements for establishing operating limits:

If you have 

an 

applicable 

emission 

limit for . 

. .

And your 

operating 

limits are 

based on . . .

You must . . 

. Using . . .

According to the 

following 

requirements

1. 

Particulate 

matter or

mercury

a. Wet scrubber 

operating 

parameters

i. Establish 

a sitespecific 

minimum 

pressure drop 

and minimum 

flow rate 

operating 

limit 

according to 

§63.7530(c)

(1) Data from 

the pressure 

drop and 

liquid flow 

rate monitors 

and the 

particulate 

matter or

mercury 

performance 

test

(a) You must 

collect pressure 

drop and liquid 

flow-rate data 

every 15 minutes 

during the 

entire period of 

the performance 

tests;

 (b) Determine 

the average 

pressure drop 

and liquid flowrate for each 

individual test 

run in the 

three-run 

performance test 

by computing the 

average of all 

the 15-minute 

readings taken 

during each test 

run.
305

 b. 

Electrostatic 

precipitator 

operating 

parameters 

(option only 

for units with 

additional wet 

scrubber 

control)

i. Establish 

a sitespecific 

minimum 

voltage and 

secondary 

current or 

total power 

input 

according to 

§63.7530(c)

(1) Data from 

the pressure 

drop and 

liquid flow 

rate monitors 

and the 

particulate 

matter or

mercury

performance 

test

(a) You must 

collect voltage 

and secondary 

current or total 

power input data 

every 15 minutes 

during the 

entire period of 

the performance 

tests;

 (b) Determine 

the average 

voltage and 

secondary 

current or total 

power input for 

each individual 

test run in the 

three-run 

performance test 

by computing the 

average of all 

the 15-minute 

readings taken 

during each test 

run.

2. Hydrogen 

Chloride

a. Wet scrubber 

operating 

parameters

i. Establish 

a sitespecific 

minimum 

pressure drop 

and minimum 

flow rate 

operating 

limit 

according to 

§63.7530(c)

(1) Data from 

the pH, 

pressure 

drop, and 

liquid flowrate monitors 

and the 

hydrogen 

chloride 

performance 

test

(a) You must 

collect pH, 

pressure drop, 

and liquid flowrate data every 

15 minutes 

during the 

entire period of 

the performance 

tests;

 (b) Determine 

the average pH, 

pressure drop, 

and liquid flowrate for each 

individual test 

run in the 

three-run 

performance test 

by computing the 

average of all 

the 15-minute 

readings taken 

during each test 

run.
306

 b. Dry scrubber 

operating 

parameters

i. Establish 

a sitespecific 

minimum 

sorbent 

injection 

rate 

operating 

limit 

according to 

§63.7530(c)

(1) Data from 

the sorbent 

injection 

rate monitors 

and hydrogen 

chloride 

performance 

test

(a) You must 

collect sorbent 

injection rate 

data every 15 

minutes during 

the entire 

period of the 

performance 

tests;

 (b) Determine 

the average 

sorbent 

injection rate 

for each 

individual test 

run in the 

three-run 

performance test 

by computing the 

average of all 

the 15-minute 

readings taken 

during each test 

run.

Table 8 to Subpart DDDDD of Part 63—Demonstrating 

Continuous Compliance

As stated in §63.7540, you must show continuous compliance 

with the emission limitations for affected sources 

according to the following:

If you must meet the 

following operating 

limits or work practice

standards . . .

You must demonstrate continuous compliance by 

. . .

1. Opacity a. Collecting the opacity monitoring system 

data according to §§63.7525(b) and 63.7535; 

and

 b. Reducing the opacity monitoring data to 6-

minute averages; and

 c. Maintaining opacity to less than or equal 

to 10 percent (daily block average).

2. Fabric Filter Bag Leak 

Detection Operation

Installing and operating a bag leak detection 

system according to §63.7525 and operating the 

fabric filter such that the requirements in 

§63.7540(a)(9) are met.
307

3. Wet Scrubber Pressure 

Drop and Liquid Flow-rate

a. Collecting the pressure drop and liquid 

flow rate monitoring system data according to 

§§63.7525 and 63.7535; and

 b. Reducing the data to 12-hour block 

averages; and

 c. Maintaining the 12-hour average pressure 

drop and liquid flow-rate at or above the 

operating limits established during the 

performance test according to §63.7530(c).

4. Wet Scrubber pH a. Collecting the pH monitoring system data 

according to §§63.7525 and 63.7535; and

 b. Reducing the data to 12-hour block 

averages; and

 c. Maintaining the 12-hour average pH at or 

above the operating limit established during 

the performance test according to §63.7530(c).

5. Dry Scrubber Sorbent 

or Carbon Injection Rate

a. Collecting the sorbent or carbon injection 

rate monitoring system data for the dry 

scrubber according to §§63.7525 and 63.7535; 

and

 b. Reducing the data to 12-hour block 

averages; and

 c. Maintaining the 12-hour average sorbent or 

carbon injection rate at or above the 

operating limit established during the 

performance test according to §§63.7530(c).

6. Electrostatic 

Precipitator Secondary 

Current and Voltage or 

Total Power Input

a. Collecting the secondary current and 

voltage or total power input monitoring system 

data for the electrostatic precipitator 

according to §§63.7525 and 63.7535; and

 b. Reducing the data to 12-hour block 

averages; and

 c. Maintaining the 12-hour average secondary 

current and voltage or total power input at or 

above the operating limits established during 

the performance test according to 

§§63.7530(c).

7. Fuel Pollutant Content a. Only burning the fuel types and fuel 

mixtures used to demonstrate compliance with 

the applicable emission limit according to 

§63.7530(c) or (d) as applicable; and

 b. Keeping monthly records of fuel use 

according to §63.7540(a).

Table 9 to Subpart DDDDD of Part 63—Reporting Requirements
308

As stated in §63.7550, you must comply with the following 

requirements for reports:

You must submit a(n)

The report must contain . . 

.

You must submit 

the report . . .

1. Compliance report a. Information required in 

§63.7550(c)(1) through (11); 

and

Semiannually 

according to the 

requirements in 

§63.7550(b).

 b. If there are no 

deviations from any emission 

limitation (emission limit 

and operating limit) that 

applies to you and there are 

no deviations from the 

requirements for work 

practice standards in Table 

8 to this subpart that apply 

to you, a statement that 

there were no deviations 

from the emission 

limitations and work 

practice standards during 

the reporting period. If 

there were no periods during 

which the CMSs, including 

continuous emissions 

monitoring system, 

continuous opacity 

monitoring system, and 

operating parameter 

monitoring systems, were 

out-of-control as specified 

in §63.8(c)(7), a statement 

that there were no periods 

during which the CMSs were 

out-of-control during the 

reporting period; and

 c. If you have a deviation 

from any emission limitation 

(emission limit and 

operating limit) or work 

practice standard during the 

reporting period, the report 

must contain the information 

in §63.7550(d). If there 

were periods during which 

the CMSs, including 

continuous emissions 

monitoring system, 

continuous opacity 

monitoring system, and 

operating parameter 
309

monitoring systems, were 

out-of-control, as specified 

in §63.8(c)(7), the report 

must contain the information 

in §63.7550(e); and

 d. If you had a startup, 

shutdown, or malfunction 

during the reporting period 

and you took actions 

consistent with your 

startup, shutdown, and 

malfunction plan, the 

compliance report must 

include the information in 

§63.10(d)(5)(i)

2. An immediate 

startup, shutdown, and 

malfunction report if 

you had a startup, 

shutdown, or 

malfunction during the 

reporting period that 

is not consistent with 

your startup, shutdown, 

and malfunction plan, 

and the source exceeds 

any applicable emission 

limitation in the 

relevant emission 

standard

a. Actions taken for the 

event; and

i. By fax or 

telephone within 2 

working days after 

starting actions 

inconsistent with 

the plan; and

 b. The information in 

§63.10(d)(5)(ii)

ii. By letter 

within 7 working 

days after the end 

of the event 

unless you have 

made alternative 

arrangements with 

the permitting 

authority.

Table 10 to Subpart DDDDD of Part 63—Applicability of 

General Provisions to Subpart DDDDD

As stated in §63.7565, you must comply with the applicable 

General Provisions according to the following:

Citation Subject Applies to subpart DDDDD

§63.1 Applicability Yes.
310

§63.2 Definitions Yes. Additional terms 

defined in §63.7575

§63.3 Units and 

Abbreviations

Yes.

§63.4 Prohibited 

Activities and 

Circumvention

Yes.

§63.5 Preconstruction 

Review and 

Notification 

Requirements

Yes

§63.6(a), (b)(1)-

(b)(5), (b)(7), 

(c), (f)(2)-(3), 

(g), (h)(2)-

(h)(9), (i), (j)

Compliance with 

Standards and 

Maintenance 

Requirements

Yes.

§63.6(e)(1), 

(e)(3), (f)(1), 

and(h)(1)

Startup, shutdown, 

and malfunction 

requirements and 

Opacity/ Visible 

Emission Limits

No. Standards apply at all 

times, including during 

startup, shutdown, and 

malfunction events.

§63.7(a), (b), 

(c), (d), (e)(2)-

(e)(9), (f), (g), 

and (h)

Performance 

Testing 

Requirements

Yes.

 

§63.7(e)(1) Conditions for 

conducting 

performance tests.

No. Subpart DDDDD 

specifies conditions for 

conducting performance 

tests at §63.7520.

§63.8 Monitoring 

Requirements

Yes.

§63.9 Notification 

Requirements

Yes. 

§63.10(a), 

(b)(1), 

(b)(2)(i)-(iii),

(b)(2)(vi)(xiv),

(c), (d)(1)-(2), 

(e), and (f) 

Recordkeeping and 

Reporting 

Requirements

Yes.
311

§63.10(b)(2)(iv)-

(v),(b)(3),and 

(d)(3)-(5)

No

§63.10(c)(15) Allows use of SSM 

plan

No.

§63.11 Control Device 

Requirements

No.

§63.12 State Authority 

and Delegation

Yes.

§63.13-63.16 Addresses, 

Incorporation by 

Reference, 

Availability of 

Information, 

Performance Track 

Provisions

Yes. 

§63.1(a)(5),(a)(7

)-(a)(9), (b)(2), 

(c)(3)-(4), (d), 

63.6(b)(6), 

(c)(3), (c)(4), 

(d), (e)(2), 

(e)(3)(ii), 

(h)(3), 

(h)(5)(iv), 

63.8(a)(3), 

63.9(b)(3), 

(h)(4), 

63.10(c)(2)-(4), 

(c)(9).

Reserved No