Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

BLR1 EU ICR Section 114 Test April 2010

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Wednesday, February 02, 2011 Page 1 of 13
BLR1 EU ICR Section 114 Test April 2010

Facility Information:

Silver Bay Power

10 Outer Drive

Silver Bay MN 55614

Contact: Mr. Scott Gischia

Phone: (218)226-6076

Fax: (218)226-6096

Email: Scott.Gischia@CliffsNR.com

Testing Company:

Barr Engineering Company

4700 W. 77th St.

Minneapolis MN 55435

Contact:Mr. Mark Petersen

Phone: (952)832-2955

Fax: (952)832-2601

Email: mpetersen@barr.com

Air Permit Number:

07500003-007

Permitted Source ID/Name:

BLR2 Power Boiler 2

Permitted Maximum Process Rate:

765 MMBtu/hr

Max. Normal Operation Process Rate:

65 MW

Target Process Test Rate

65 MW

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

517 MMBtu/hr steam boiler. Produces steam for a 45 MW/hr electric turbine

Industry/SCC/NAIS 212210

Sampling Location Information:

Test Parameter Information:

AFS #: FRS #:

SCC / Description 10100222 External Combustion Boilers - Electric Generation - Bituminous/Subbituminous 

Coal - Pulverized Coal: Dry Bottom (Subbituminous Coal) 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack - 48 113 0 0 8.98 45 55 2 48

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack - 48 2,3,7,8-TCDD Method 23 3 480 0

Stack - 48 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack - 48 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack - 48 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack - 48 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack - 48 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack - 48 OCDD Method 23 3 480 0

Wednesday, February 02, 2011 Page 2 of 13
BLR1 EU ICR Section 114 Test April 2010

The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Stack - 48 2,3,7,8-TCDF Method 23 3 480 0

Stack - 48 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack - 48 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack - 48 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack - 48 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack - 48 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack - 48 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack - 48 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack - 48 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack - 48 OCDF Method 23 3 480 0

Stack - 48 Other TCDD Method 23 3 480 0

Stack - 48 Other PeCDD Method 23 3 480 0

Stack - 48 Other HxCDD Method 23 3 480 0

Stack - 48 Other HpCDD Method 23 3 480 0

Stack - 48 Other TCDF Method 23 3 480 0

Stack - 48 Other PeCDF Method 23 3 480 0

Stack - 48 Other HxCDF Method 23 3 480 0

Stack - 48 Other HpCDF Method 23 3 480 0

Stack - 48 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack - 48 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack - 48 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack - 48 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack - 48 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack - 48 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack - 48 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack - 48 Method 23 3 480 0

Stack - 48 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack - 48 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack - 48 Method 23 3 480 0

Wednesday, February 02, 2011 Page 3 of 13
BLR1 EU ICR Section 114 Test April 2010

Sampling / Stack Data Results Summary

Location Stack - 48 - Method 23

Average

Run Number 1 2 3

Test Date 3/23/2010 3/24/2010 3/25/2010

Run Start Time 9:11:00 AM 9:07:00 

AM

6:39:00 AM

Run Finish Time 5:18:00 PM 5:19:00 PM 4:35:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 302.176 308.403 302.686 304.422

Moisture Content of Stack Gas, % 10.96 10.92 10.98 10.953

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 14.3 13.7 13.9 13.967

Oxygen, % 5.6 6.1 5.9 5.867

Average Stack Gas Temperature, °F 305.46 304.15 303.17 304.260

Dry Volumetric Flow Rate, dry scfm 167,331.3 172,799.4 170,335.1 170,155.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 280,219.6 286,780.1 281,556.8 282,852.167

Percent Isokinetic of Sampling Rate, % 102.0 100.8 100.4 101.067

F-Factor, dscfm/MMBtu @ %O2 9883 9883 9883 9,883.000

Fw 11700 11800 11800 11,766.667

Fc 1800 1800 1800 1,800.000

Wednesday, February 02, 2011 Page 4 of 13
BLR1 EU ICR Section 114 Test April 2010

Emissions Summary

Location: Stack - 48 - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000209 0.0000013 0.00000368 0.000

lb/mmBtuO2 2.06E-10 1.30E-10 3.69E-10 0.000

ng/dscm 2.44E-01 1.49E-01 4.29E-01 0.274

ng/dscm@7%O2 2.22E-01 1.40E-01 3.98E-01 0.253

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000983 0.00000000552 0.0000000361 0.000

lb/mmBtuO2 9.68E-13 5.51E-13 3.62E-12 0.000

ng/dscm 1.15E-03 6.32E-04 4.21E-03 0.002

ng/dscm@7%O2 1.04E-03 5.94E-04 3.90E-03 0.002

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000206 0.000000012 0.0000000463 0.000

lb/mmBtuO2 2.03E-12 1.20E-12 4.64E-12 0.000

ng/dscm 2.41E-03 1.37E-03 5.40E-03 0.003

ng/dscm@7%O2 2.19E-03 1.29E-03 5.00E-03 0.003

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000166 0.0000000904 0.000000302 0.000

lb/mmBtuO2 1.64E-11 9.02E-12 3.03E-11 0.000

ng/dscm 1.94E-02 1.04E-02 3.52E-02 0.022

ng/dscm@7%O2 1.76E-02 9.77E-03 3.26E-02 0.020

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000762 0.0000000485 0.000000154 0.000

lb/mmBtuO2 7.51E-12 4.84E-12 1.54E-11 0.000

ng/dscm 8.91E-03 5.55E-03 1.80E-02 0.011

ng/dscm@7%O2 8.09E-03 5.21E-03 1.67E-02 0.010

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000121 0.000000721 0.00000213 0.000

lb/mmBtuO2 1.19E-10 7.19E-11 2.14E-10 0.000

ng/dscm 1.41E-01 8.26E-02 2.49E-01 0.158

ng/dscm@7%O2 1.28E-01 7.76E-02 2.31E-01 0.146

Compound: 1,2,3,6,7,8-HxCDF

Average

Wednesday, February 02, 2011 Page 5 of 13
BLR1 EU ICR Section 114 Test April 2010

RunNumber 1 2 3

Mass_mg 0.0000000665 0.0000000426 0.000000124 0.000

lb/mmBtuO2 6.55E-12 4.25E-12 1.24E-11 0.000

ng/dscm 7.77E-03 4.88E-03 1.45E-02 0.009

ng/dscm@7%O2 7.06E-03 4.58E-03 1.34E-02 0.008

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000436 0.00000025 0.000000771 0.000

lb/mmBtuO2 4.29E-11 2.49E-11 7.73E-11 0.000

ng/dscm 5.10E-02 2.86E-02 9.00E-02 0.057

ng/dscm@7%O2 4.63E-02 2.69E-02 8.34E-02 0.052

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000634 0.0000000385 0.000000121 0.000

lb/mmBtuO2 6.24E-12 3.84E-12 1.21E-11 0.000

ng/dscm 7.41E-03 4.41E-03 1.41E-02 0.009

ng/dscm@7%O2 6.73E-03 4.14E-03 1.31E-02 0.008

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000423 0.0000000262 0.000000077 0.000

lb/mmBtuO2 4.17E-12 2.61E-12 7.72E-12 0.000

ng/dscm 4.94E-03 3.00E-03 8.99E-03 0.006

ng/dscm@7%O2 4.49E-03 2.82E-03 8.33E-03 0.005

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000107 0.000000667 0.00000196 0.000

lb/mmBtuO2 1.05E-10 6.65E-11 1.97E-10 0.000

ng/dscm 1.25E-01 7.64E-02 2.29E-01 0.143

ng/dscm@7%O2 1.14E-01 7.18E-02 2.12E-01 0.133

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.000000012 0.0000000104 0.0000000233 0.000

lb/mmBtuO2 1.18E-12 1.04E-12 2.34E-12 0.000

ng/dscm 1.40E-03 1.19E-03 2.72E-03 0.002

ng/dscm@7%O2 1.27E-03 1.12E-03 2.52E-03 0.002

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000295 0.000000268 0.000000296 0.000

lb/mmBtuO2 2.91E-11 2.67E-11 2.97E-11 0.000

ng/dscm 3.45E-02 3.07E-02 3.45E-02 0.033

ng/dscm@7%O2 3.13E-02 2.88E-02 3.20E-02 0.031

Wednesday, February 02, 2011 Page 6 of 13
BLR1 EU ICR Section 114 Test April 2010

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.00000231 0.00000207 0.00000332 0.000

lb/mmBtuO2 2.28E-10 2.07E-10 3.33E-10 0.000

ng/dscm 2.70E-01 2.37E-01 3.87E-01 0.298

ng/dscm@7%O2 2.45E-01 2.23E-01 3.59E-01 0.276

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.000000117 0.000000108 0.000000101 0.000

lb/mmBtuO2 1.15E-11 1.08E-11 1.01E-11 0.000

ng/dscm 1.37E-02 1.24E-02 1.18E-02 0.013

ng/dscm@7%O2 1.24E-02 1.16E-02 1.09E-02 0.012

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.000000215 0.000000206 0.000000363 0.000

lb/mmBtuO2 2.12E-11 2.06E-11 3.64E-11 0.000

ng/dscm 2.51E-02 2.36E-02 4.24E-02 0.030

ng/dscm@7%O2 2.28E-02 2.22E-02 3.93E-02 0.028

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000725 0.00000631 0.0000109 0.000

lb/mmBtuO2 7.14E-10 6.30E-10 1.09E-09 0.000

ng/dscm 8.47E-01 7.23E-01 1.27E+00 0.947

ng/dscm@7%O2 7.69E-01 6.79E-01 1.18E+00 0.876

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.000000163 0.000000118 0.00000022 0.000

lb/mmBtuO2 1.61E-11 1.18E-11 2.21E-11 0.000

ng/dscm 1.91E-02 1.35E-02 2.57E-02 0.019

ng/dscm@7%O2 1.74E-02 1.27E-02 2.38E-02 0.018

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000664 0.00000000366 0.0000000167 0.000

lb/mmBtuO2 6.54E-13 3.65E-13 1.67E-12 0.000

ng/dscm 7.76E-04 4.19E-04 1.95E-03 0.001

ng/dscm@7%O2 7.05E-04 3.94E-04 1.81E-03 0.001

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000011 0.0000000689 0.000000192 0.000

lb/mmBtuO2 1.08E-11 6.87E-12 1.93E-11 0.000

Wednesday, February 02, 2011 Page 7 of 13
BLR1 EU ICR Section 114 Test April 2010

ng/dscm 1.29E-02 7.89E-03 2.24E-02 0.014

ng/dscm@7%O2 1.17E-02 7.41E-03 2.08E-02 0.013

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000000393 0.00000000419 0.00000000549 0.000

lb/mmBtuO2 3.87E-13 4.18E-13 5.51E-13 0.000

ng/dscm 4.59E-04 4.80E-04 6.41E-04 0.001

ng/dscm@7%O2 4.17E-04 4.51E-04 5.94E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000514 0.000000325 0.000000927 0.000

lb/mmBtuO2 5.06E-11 3.24E-11 9.30E-11 0.000

ng/dscm 6.01E-02 3.72E-02 1.08E-01 0.068

ng/dscm@7%O2 5.46E-02 3.49E-02 1.00E-01 0.063

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000000725 0.00000000928 0.0000000239 0.000

lb/mmBtuO2 7.14E-13 9.26E-13 2.40E-12 0.000

ng/dscm 8.47E-04 1.06E-03 2.79E-03 0.002

ng/dscm@7%O2 7.69E-04 9.96E-04 2.59E-03 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000703 0.0000000399 0.000000118 0.000

lb/mmBtuO2 6.92E-12 3.98E-12 1.18E-11 0.000

ng/dscm 8.22E-03 4.57E-03 1.38E-02 0.009

ng/dscm@7%O2 7.47E-03 4.29E-03 1.28E-02 0.008

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000021 0.00000165 0.00000339 0.000

lb/mmBtuO2 2.07E-10 1.65E-10 3.40E-10 0.000

ng/dscm 2.45E-01 1.89E-01 3.96E-01 0.277

ng/dscm@7%O2 2.23E-01 1.78E-01 3.67E-01 0.256

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.000000227 0.00000018 0.000000412 0.000

lb/mmBtuO2 2.24E-11 1.80E-11 4.13E-11 0.000

ng/dscm 2.65E-02 2.06E-02 4.81E-02 0.032

ng/dscm@7%O2 2.41E-02 1.93E-02 4.46E-02 0.029

Compound: OCDD

Average

RunNumber 1 2 3

Wednesday, February 02, 2011 Page 8 of 13
BLR1 EU ICR Section 114 Test April 2010

Mass_mg 0.000000162 0.0000000899 0.000000259 0.000

lb/mmBtuO2 1.60E-11 8.97E-12 2.60E-11 0.000

ng/dscm 1.89E-02 1.03E-02 3.02E-02 0.020

ng/dscm@7%O2 1.72E-02 9.67E-03 2.80E-02 0.018

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000000757 0.00000000389 0.000000153 0.000

lb/mmBtuO2 7.46E-13 3.88E-13 1.53E-11 0.000

ng/dscm 8.85E-04 4.46E-04 1.79E-02 0.006

ng/dscm@7%O2 8.04E-04 4.19E-04 1.66E-02 0.006

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000385 0.00000242 0.0000068 0.000

lb/mmBtuO2 3.79E-10 2.41E-10 6.82E-10 0.000

ng/dscm 4.50E-01 2.77E-01 7.93E-01 0.507

ng/dscm@7%O2 4.09E-01 2.60E-01 7.35E-01 0.468

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000359 0.0000000175 0.0000000824 0.000

lb/mmBtuO2 3.54E-12 1.75E-12 8.26E-12 0.000

ng/dscm 4.20E-03 2.00E-03 9.62E-03 0.005

ng/dscm@7%O2 3.82E-03 1.88E-03 8.91E-03 0.005

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000012 0.00000712 0.0000215 0.000

lb/mmBtuO2 1.18E-09 7.10E-10 2.16E-09 0.000

ng/dscm 1.40E+00 8.15E-01 2.51E+00 1.575

ng/dscm@7%O2 1.27E+00 7.65E-01 2.33E+00 1.455

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000297 0.000000196 0.000000599 0.000

lb/mmBtuO2 2.93E-11 1.96E-11 6.01E-11 0.000

ng/dscm 3.47E-02 2.24E-02 6.99E-02 0.042

ng/dscm@7%O2 3.15E-02 2.10E-02 6.48E-02 0.039

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.00000329 0.00000219 0.00000627 0.000

lb/mmBtuO2 3.24E-10 2.18E-10 6.29E-10 0.000

ng/dscm 3.85E-01 2.51E-01 7.32E-01 0.456

ng/dscm@7%O2 3.50E-01 2.36E-01 6.78E-01 0.421

Wednesday, February 02, 2011 Page 9 of 13
BLR1 EU ICR Section 114 Test April 2010

Process Run Data

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000198 0.00000122 0.00000364 0.000

lb/mmBtuO2 1.95E-10 1.22E-10 3.65E-10 0.000

ng/dscm 2.31E-01 1.40E-01 4.25E-01 0.265

ng/dscm@7%O2 2.10E-01 1.31E-01 3.94E-01 0.245

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000456 0.000000281 0.000000796 0.000

lb/mmBtuO2 4.49E-11 2.80E-11 7.98E-11 0.000

ng/dscm 5.33E-02 3.22E-02 9.29E-02 0.059

ng/dscm@7%O2 4.84E-02 3.02E-02 8.61E-02 0.055

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000208 0.00000133 0.00000376 0.000

lb/mmBtuO2 2.05E-10 1.33E-10 3.77E-10 0.000

ng/dscm 2.43E-01 1.52E-01 4.39E-01 0.278

ng/dscm@7%O2 2.21E-01 1.43E-01 4.07E-01 0.257

Wednesday, February 02, 2011 Page 10 of 13
BLR1 EU ICR Section 114 Test April 2010

Process Run Data

APCD Run Data

Process Lab Run Data

Run Name Value UOM Comments

Target

Value

1 Subbituminous Coal Burned 42.3 Tons/hr 45

2 Subbituminous Coal Burned 41 Tons/hr 45

3 Subbituminous Coal Burned 44 Tons/hr 45

4 Subbituminous Coal Burned 0 Tons/hr 45

5 Subbituminous Coal Burned 0 Tons/hr 45

6 Subbituminous Coal Burned 0 Tons/hr 45

7 Subbituminous Coal Burned 0 Tons/hr 45

1 Heat Input 827 MMBtu/hr 765

1 Steam Output 10919 1000lb steam/hr 11400

Run Name Value UOM Comments

Target

Value

1 BAGHOUSE 1.7 in. H2O 2

2 BAGHOUSE 1.7 in. H2O 2

Run Name Value UOM Comments

1 Coal Heating value 11700 Btu/lb

2 Coal Heating value 11800 Btu/lb

1 Chloride 101 mg/Kg

2 Chloride 111 mg/Kg

1 Fluoride 55 mg/Kg

2 Fluoride 47 mg/Kg

1 mercury 48.7 ng/g

2 mercury 40 ng/g

1 Antimony

antimony

1.1 mg/Kg

2 Antimony

antimony

1.1 mg/Kg

1 Arsenic 1.1 mg/Kg

2 Arsenic 1.1 mg/Kg

1 Beryllium 0.31 mg/Kg

2 Beryllium 0.25 mg/Kg

1 Cadmium 0.04 mg/Kg

2 Cadmium 0.03 mg/Kg

1 Chromium 3.2 mg/Kg

2 Chromium 2.7 mg/Kg

Wednesday, February 02, 2011 Page 11 of 13
BLR1 EU ICR Section 114 Test April 2010

1 Cobalt 1.9 mg/Kg

2 Cobalt 1.65 mg/Kg

1 Lead 2.8 mg/Kg

2 Lead 1.95 mg/Kg

1 Manganese 14.8 mg/Kg

2 Manganese 7.15 mg/Kg

1 Nickel 4.2 mg/Kg

2 Nickel 4 mg/Kg

1 Selemium 1.1 mg/Kg

2 Selemium 1.1 mg/Kg

Wednesday, February 02, 2011 Page 12 of 13
BLR1 EU ICR Section 114 Test April 2010

Sampling / Stack Data Results Detail

Location Stack - 48 - Method 23

Average

Run Number 1 2 3

Test Date 3/23/2010 3/24/2010 3/25/2010

Run Start Time 9:11:00 AM 9:07:00 AM 6:39:00 AM

Run Finish Time 5:18:00 PM 5:19:00 PM 4:35:00 PM

Net Traversing Points 48 48 48

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.217 0.217 0.217 0.217

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.9992 0.9992 0.9992 0.999

Barometric Pressure, inches of Mercury 29.15 29.35 29.45 29.317

Average Orifice Meter Differential, inches H2O 1.37 1.40 1.32 1.363

Dry Gas Meter Volume Sampled, cubic feet 318.740 319.750 304.980 314.490

Average Dry Gas Meter Temperature, °F 84.05 78.45 64.95 75.817

Dry Gas Meter Volume Sampled, dscf 302.176 308.403 302.686 304.422

Total Moisture Liquid collected, g 790 803 793 795.333

Volume of Water Vapor, standard cubic feet 37.19 37.80 37.33 37.440

Moisture Content of Stack Gas, % 10.96 10.92 10.98 10.953

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8904 0.8908 0.8902 0.890

Carbon Dioxide, % 14.3 13.7 13.9 13.967

Oxygen, % 5.6 6.1 5.9 5.867

Carbon Monoxide & Nitrogen, % 80.1 80.2 80.2 80.167

Fuel Factor 1.07 1.08 1.08

Dry Molecular Weight, lb/lb-Mole 30.51 30.44 30.46 30.470

Wet Molecular weight, lb/lb-Mole 29.14 29.08 29.09 29.103

Flue Gas Static Pressure, inches of H2O -0.85 -0.85 -0.85 -0.850

Absolute Flue Gas Pressure, inches of Mercury 29.09 29.29 29.39 29.257

Average Stack Gas Temperature, °F 305.46 304.15 303.17 304.260

Average Velocity Head, inches of H2O 0.9658535822

37183

1.017988207

13662

0.986168956

780717

0.990

Average Stack Gas Velocity, feet/second 67.06 68.63 67.38 67.690

Stack Cross-Sectional Area, square feet 69.644 69.644 69.644 69.644

Dry Volumetric Flow Rate, dry scfm 167,331.3 172,799.4 170,335.1 170,155.267

Actual Wet Volumetric Flue Gas Flow Rate, acfm 280,219.6 286,780.1 281,556.8 282,852.167

Percent Isokinetic of Sampling Rate, % 102.0 100.8 100.4 101.067

Percent Excess Air, % 36.0 40.5 38.6 38.367

F-Factor, dscfm/MMBtu @ %O2 9883 9883 9883 9,883.000

Round Duct Diameter, inches 113 113 113

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 11700 11800 11800 11,766.667

Fc 1800 1800 1800 1,800.000

Wednesday, February 02, 2011 Page 13 of 13