Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, March 07, 2011 Page 1 of 20
Facility Information:

PREPA Aguirre Power Station

Road PR-03 Km 152.7

Bo. Montesoria, Aguirre

Salinas PR 00704-0317

Contact: Arsenio Reyes

Phone: 787-521-4988

Fax: 787-521-4805

Email: a-reyes-ddpa@prepa.com

Testing Company:

URS Corporation

Richard McMillan, PE

1600 Perimeter Park Dr.

Morrisville NC 27560

Contact: Field test leader

Phone: Of above person

Fax: 919-461-1217

Email: Richard_McMillan@URSCorp.com

Air Permit Number:

Enter your facilities ORIS Number here

Permitted Source ID/Name:

AG2 Enter the Boiler ID of the tested boiler (left)

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

This description should describe the process and associated controls to differentiate this facility from, or document 

similarity with others of same SCC.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: Enter ARS ID FRS #: Enter FRS ID

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Tangential Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 0 0 0 0 0 0 0 0

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Monday, March 07, 2011 Page 2 of 20
Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Stack Exit Total PCBs Method 23 3 480 0

Stack Exit Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Monday, March 07, 2011 Page 3 of 20
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

In this section, identify the promulgation date of any specified test method that you use for determining the 

procedures followed. This field is also used to document any modifications that are necessary to conduct the 

emissions test if they are outside the requirements of the cited method. If this modification was approved verbally by 

a regulatory agency, the name and date of approval should be included. Written formal approval should be attached 

to this file using the "Attach File" button. Test procedures that are different from those published in the Federal 

Register should be attached using the "Attach File" button.

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Co2 Method 3A CO2 3 120 0

Stack Exit Co2 Method 3A CO2 3 240 0

Stack Exit O2 Method 3A O2 3 240 0

Stack Exit O2 Method 3A O2 3 480 0

Stack Exit Co2 Method 3A CO2 3 480 0

Stack Exit O2 Method 3A O2 3 120 0

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Filterable Particulate Method 5 3 240 0

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Monday, March 07, 2011 Page 4 of 20
Sampling / Stack Data Results Summary

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 9/21/2010 9/27/2010 9/28/2010

Run Start Time 10:15:00 AM 10:05:00 

AM

10:00:00 AM

Run Finish Time 7:33:00 PM 6:53:00 PM 6:38:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 302.232 299.654 308.416 303.434

Moisture Content of Stack Gas, % 12.45 12.48 12.51 12.480

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 11.1 13 13.5 12.533

Oxygen, % 6 4.7 4 4.900

Average Stack Gas Temperature, °F 310.79 304.96 307.13 307.627

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 100.5 101.7 102.6 101.600

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 5 of 20
Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 9/13/2010 9/14/2010 9/15/2010

Run Start Time 4:00:00 PM 1:05:00 PM 9:55:00 AM

Run Finish Time 8:00:00 PM 5:15:00 PM 2:05:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 145.782 142.279 145.644 144.568

Moisture Content of Stack Gas, % 12.46 12.87 12.64 12.657

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.2 13.8 13.4 13.467

Oxygen, % 4.5 3.8 4.2 4.167

Average Stack Gas Temperature, °F 310.00 309.83 307.83 309.220

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 97.2 97.4 97.9 97.500

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 9/13/2010 9/14/2010 9/15/2010

Run Start Time 10:20:00 AM 1:00:00 PM 9:56:00 AM

Run Finish Time 4:41:30 PM 4:09:00 PM 1:00:00 PM

Net Run Time, minutes 122.25 118.25 117.25

Dry Gas Meter Volume Sampled, dscf 41.653 40.442 40.093 40.729

Moisture Content of Stack Gas, % 12.72 12.28 12.41 12.470

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 13.2 13.7 13.7 13.533

Oxygen, % 4.5 3.8 3.9 4.067

Average Stack Gas Temperature, °F 310.92 312.83 308.79 310.847

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 98.0 101.3 101.4 100.233

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 6 of 20
Emissions Summary

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000052 0.000000002 0.0000000034 0.000

lb/mmBtuO2 4.89E-13 1.74E-13 2.76E-13 0.000

ng/dscm 6.08E-04 2.36E-04 3.89E-04 0.000

ng/dscm@7%O2 5.67E-04 2.02E-04 3.20E-04 0.000

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000051 0.0000000041 0.0000000032 0.000

lb/mmBtuO2 4.80E-13 3.58E-13 2.60E-13 0.000

ng/dscm 5.96E-04 4.83E-04 3.66E-04 0.000

ng/dscm@7%O2 5.56E-04 4.14E-04 3.01E-04 0.000

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.0000000017 0.000000002 0.000

lb/mmBtuO2 1.60E-13 1.48E-13 1.62E-13 0.000

ng/dscm 1.99E-04 2.00E-04 2.29E-04 0.000

ng/dscm@7%O2 1.86E-04 1.72E-04 1.88E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000016 0.000000002 0.0000000022 0.000

lb/mmBtuO2 1.50E-13 1.74E-13 1.79E-13 0.000

ng/dscm 1.87E-04 2.36E-04 2.52E-04 0.000

ng/dscm@7%O2 1.74E-04 2.02E-04 2.07E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000047 0.0000000026 0.0000000032 0.000

lb/mmBtuO2 4.42E-13 2.27E-13 2.60E-13 0.000

ng/dscm 5.49E-04 3.06E-04 3.66E-04 0.000

ng/dscm@7%O2 5.12E-04 2.63E-04 3.01E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000014 0.000000002 0.0000000021 0.000

lb/mmBtuO2 1.32E-13 1.74E-13 1.71E-13 0.000

ng/dscm 1.64E-04 2.36E-04 2.40E-04 0.000

ng/dscm@7%O2 1.53E-04 2.02E-04 1.97E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Monday, March 07, 2011 Page 7 of 20
RunNumber 1 2 3

Mass_mg 0.0000000076 0.0000000046 0.0000000059 0.000

lb/mmBtuO2 7.15E-13 4.01E-13 4.79E-13 0.000

ng/dscm 8.88E-04 5.42E-04 6.76E-04 0.001

ng/dscm@7%O2 8.28E-04 4.65E-04 5.56E-04 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.0000000021 0.0000000023 0.000

lb/mmBtuO2 1.60E-13 1.83E-13 1.87E-13 0.000

ng/dscm 1.99E-04 2.48E-04 2.63E-04 0.000

ng/dscm@7%O2 1.86E-04 2.13E-04 2.16E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000016 0.0000000018 0.0000000017 0.000

lb/mmBtuO2 1.50E-13 1.57E-13 1.38E-13 0.000

ng/dscm 1.87E-04 2.12E-04 1.95E-04 0.000

ng/dscm@7%O2 1.74E-04 1.82E-04 1.60E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000027 0.0000000026 0.0000000025 0.000

lb/mmBtuO2 2.54E-13 2.27E-13 2.03E-13 0.000

ng/dscm 3.16E-04 3.06E-04 2.86E-04 0.000

ng/dscm@7%O2 2.95E-04 2.63E-04 2.35E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000058 0.0000000038 0.000000003 0.000

lb/mmBtuO2 5.45E-13 3.31E-13 2.44E-13 0.000

ng/dscm 6.78E-04 4.48E-04 3.44E-04 0.000

ng/dscm@7%O2 6.32E-04 3.84E-04 2.83E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000081 0.0000000159 0.0000000084 0.000

lb/mmBtuO2 7.62E-13 1.39E-12 6.82E-13 0.000

ng/dscm 9.47E-04 1.87E-03 9.62E-04 0.001

ng/dscm@7%O2 8.83E-04 1.60E-03 7.91E-04 0.001

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.000000137 0.000000362 0.000000148 0.000

lb/mmBtuO2 1.29E-11 3.16E-11 1.20E-11 0.000

ng/dscm 1.60E-02 4.27E-02 1.69E-02 0.025

ng/dscm@7%O2 1.49E-02 3.66E-02 1.39E-02 0.022

Monday, March 07, 2011 Page 8 of 20
Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000301 0.000000682 0.000000321 0.000

lb/mmBtuO2 2.83E-11 5.95E-11 2.61E-11 0.000

ng/dscm 3.52E-02 8.04E-02 3.68E-02 0.051

ng/dscm@7%O2 3.28E-02 6.90E-02 3.03E-02 0.044

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000604 0.000000178 0.0000000734 0.000

lb/mmBtuO2 5.68E-12 1.55E-11 5.96E-12 0.000

ng/dscm 7.06E-03 2.10E-02 8.41E-03 0.012

ng/dscm@7%O2 6.59E-03 1.80E-02 6.92E-03 0.011

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000171 0.0000000423 0.0000000204 0.000

lb/mmBtuO2 1.61E-12 3.69E-12 1.66E-12 0.000

ng/dscm 2.00E-03 4.99E-03 2.34E-03 0.003

ng/dscm@7%O2 1.87E-03 4.28E-03 1.92E-03 0.003

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.00000108 0.00000294 0.00000126 0.000

lb/mmBtuO2 1.02E-10 2.56E-10 1.02E-10 0.000

ng/dscm 1.26E-01 3.47E-01 1.44E-01 0.206

ng/dscm@7%O2 1.18E-01 2.98E-01 1.18E-01 0.178

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000131 0.0000000268 0.0000000168 0.000

lb/mmBtuO2 1.23E-12 2.34E-12 1.36E-12 0.000

ng/dscm 1.53E-03 3.16E-03 1.92E-03 0.002

ng/dscm@7%O2 1.43E-03 2.71E-03 1.58E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000061 0.0000000033 0.0000000041 0.000

lb/mmBtuO2 5.74E-13 2.88E-13 3.33E-13 0.000

ng/dscm 7.13E-04 3.89E-04 4.70E-04 0.001

ng/dscm@7%O2 6.65E-04 3.34E-04 3.87E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000122 0.0000000078 0.0000000081 0.000

lb/mmBtuO2 1.15E-12 6.80E-13 6.58E-13 0.000

Monday, March 07, 2011 Page 9 of 20
ng/dscm 1.43E-03 9.19E-04 9.28E-04 0.001

ng/dscm@7%O2 1.33E-03 7.89E-04 7.63E-04 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000019 0.0000000021 0.0000000023 0.000

lb/mmBtuO2 1.79E-13 1.83E-13 1.87E-13 0.000

ng/dscm 2.22E-04 2.48E-04 2.63E-04 0.000

ng/dscm@7%O2 2.07E-04 2.13E-04 2.16E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000043 0.0000000032 0.0000000025 0.000

lb/mmBtuO2 4.04E-13 2.79E-13 2.03E-13 0.000

ng/dscm 5.03E-04 3.77E-04 2.86E-04 0.000

ng/dscm@7%O2 4.69E-04 3.23E-04 2.35E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000069 0.0000000181 0.0000000097 0.000

lb/mmBtuO2 6.49E-13 1.58E-12 7.88E-13 0.000

ng/dscm 8.06E-04 2.13E-03 1.11E-03 0.001

ng/dscm@7%O2 7.52E-04 1.83E-03 9.13E-04 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000053 0.0000000143 0.0000000064 0.000

lb/mmBtuO2 4.98E-13 1.25E-12 5.20E-13 0.000

ng/dscm 6.19E-04 1.69E-03 7.33E-04 0.001

ng/dscm@7%O2 5.77E-04 1.45E-03 6.03E-04 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.000000131 0.000000398 0.000000159 0.000

lb/mmBtuO2 1.23E-11 3.47E-11 1.29E-11 0.000

ng/dscm 1.53E-02 4.69E-02 1.82E-02 0.027

ng/dscm@7%O2 1.43E-02 4.02E-02 1.50E-02 0.023

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000000043 0.0000000098 0.0000000045 0.000

lb/mmBtuO2 4.04E-13 8.55E-13 3.66E-13 0.000

ng/dscm 5.03E-04 1.16E-03 5.15E-04 0.001

ng/dscm@7%O2 4.69E-04 9.95E-04 4.24E-04 0.001

Compound: OCDD

Average

RunNumber 1 2 3

Monday, March 07, 2011 Page 10 of 20
Mass_mg 0.0000000104 0.0000000102 0.000000011 0.000

lb/mmBtuO2 9.78E-13 8.90E-13 8.94E-13 0.000

ng/dscm 1.22E-03 1.20E-03 1.26E-03 0.001

ng/dscm@7%O2 1.14E-03 1.03E-03 1.04E-03 0.001

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000033 0.0000000041 0.000

lb/mmBtuO2 3.01E-13 2.88E-13 3.33E-13 0.000

ng/dscm 3.74E-04 3.89E-04 4.70E-04 0.000

ng/dscm@7%O2 3.49E-04 3.34E-04 3.87E-04 0.000

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000051 0.0000000053 0.0000000041 0.000

lb/mmBtuO2 4.80E-13 4.62E-13 3.33E-13 0.000

ng/dscm 5.96E-04 6.25E-04 4.70E-04 0.001

ng/dscm@7%O2 5.56E-04 5.36E-04 3.87E-04 0.000

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000031 0 0 0.000

lb/mmBtuO2 2.91E-13 0.00E+00 0.00E+00 0.000

ng/dscm 3.62E-04 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 3.38E-04 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000158 0.0000000096 0.0000000128 0.000

lb/mmBtuO2 1.49E-12 8.37E-13 1.04E-12 0.000

ng/dscm 1.85E-03 1.13E-03 1.47E-03 0.001

ng/dscm@7%O2 1.73E-03 9.70E-04 1.21E-03 0.001

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000215 0.0000000094 0.0000000109 0.000

lb/mmBtuO2 2.02E-12 8.20E-13 8.86E-13 0.000

ng/dscm 2.51E-03 1.11E-03 1.25E-03 0.002

ng/dscm@7%O2 2.34E-03 9.52E-04 1.03E-03 0.001

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000158 0.0000000087 0 0.000

lb/mmBtuO2 1.49E-12 7.59E-13 0.00E+00 0.000

ng/dscm 1.85E-03 1.03E-03 0.00E+00 0.001

ng/dscm@7%O2 1.73E-03 8.84E-04 0.00E+00 0.001

Monday, March 07, 2011 Page 11 of 20
Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000921 0.0000000593 0.000000056 0.000

lb/mmBtuO2 8.66E-12 5.17E-12 4.55E-12 0.000

ng/dscm 1.08E-02 6.99E-03 6.41E-03 0.008

ng/dscm@7%O2 1.01E-02 6.00E-03 5.27E-03 0.007

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000189 0.0000000182 0.0000000146 0.000

lb/mmBtuO2 1.78E-12 1.59E-12 1.19E-12 0.000

ng/dscm 2.21E-03 2.15E-03 1.67E-03 0.002

ng/dscm@7%O2 2.06E-03 1.84E-03 1.37E-03 0.002

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000232 0.000000148 0.00000014 0.000

lb/mmBtuO2 2.18E-11 1.29E-11 1.14E-11 0.000

ng/dscm 2.71E-02 1.74E-02 1.60E-02 0.020

ng/dscm@7%O2 2.53E-02 1.49E-02 1.32E-02 0.018

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.0000000805 0.0000000647 0.0000000573 0.000

lb/mmBtuO2 7.57E-12 5.64E-12 4.66E-12 0.000

ng/dscm 9.41E-03 7.63E-03 6.56E-03 0.008

ng/dscm@7%O2 8.78E-03 6.55E-03 5.40E-03 0.007

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.000000401 0.0000002528 0.0000002446 0.000

lb/mmBtuO2 3.77E-11 2.21E-11 1.99E-11 0.000

ng/dscm 4.69E-02 2.98E-02 2.80E-02 0.035

ng/dscm@7%O2 4.38E-02 2.56E-02 2.30E-02 0.031

Compound: Total PCBs

Average

RunNumber 1 2 3

Mass_mg 0.0000017643 0.0000046872 0.0000020276 0.000

lb/mmBtuO2 1.66E-10 4.09E-10 1.65E-10 0.000

ng/dscm 2.06E-01 5.52E-01 2.32E-01 0.330

ng/dscm@7%O2 1.92E-01 4.74E-01 1.91E-01 0.286

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

Monday, March 07, 2011 Page 12 of 20
ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Location: Stack Exit - Method 29 

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.39924 0.41708 0.354 0.390

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 7.07E-05 7.26E-05 6.16E-05 0.000

mg/dscm 9.67E-02 1.04E-01 8.58E-02 0.096

mg/dscm@7%O2 8.20E-02 8.45E-02 7.14E-02 0.079

Compound: Arsenic

Average

RunNumber 1 2 3

Mass_mg 0.02711 0.02783 0.0265 0.027

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 4.80E-06 4.84E-06 4.61E-06 0.000

mg/dscm 6.57E-03 6.91E-03 6.43E-03 0.007

mg/dscm@7%O2 5.57E-03 5.62E-03 5.35E-03 0.006

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.001512 0.001412 0.0013 0.001

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 2.68E-07 2.46E-07 2.26E-07 0.000

mg/dscm 3.66E-04 3.51E-04 3.15E-04 0.000

mg/dscm@7%O2 3.10E-04 2.85E-04 2.62E-04 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.002481 0.00233 0.0047 0.003

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 4.39E-07 4.06E-07 8.18E-07 0.000

mg/dscm 6.01E-04 5.78E-04 1.14E-03 0.001

mg/dscm@7%O2 5.09E-04 4.70E-04 9.49E-04 0.001

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.0848 0.0264 0.035 0.049

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 1.50E-05 4.59E-06 6.09E-06 0.000

mg/dscm 2.05E-02 6.55E-03 8.49E-03 0.012

mg/dscm@7%O2 1.74E-02 5.32E-03 7.07E-03 0.010

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 380.5 315.9 291.7 329.367

Monday, March 07, 2011 Page 13 of 20
Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 6.74E-02 5.50E-02 5.08E-02 0.058

mg/dscm 9.22E+01 7.84E+01 7.07E+01 80.433

mg/dscm@7%O2 7.81E+01 6.37E+01 5.88E+01 66.867

Compound: Lead

Average

RunNumber 1 2 3

Mass_mg 0.0636 0.0731 0.0475 0.061

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 1.13E-05 1.27E-05 8.27E-06 0.000

mg/dscm 1.54E-02 1.81E-02 1.15E-02 0.015

mg/dscm@7%O2 1.31E-02 1.47E-02 9.57E-03 0.012

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.2251 0.1863 0.187 0.199

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 3.99E-05 3.24E-05 3.26E-05 0.000

mg/dscm 5.45E-02 4.62E-02 4.53E-02 0.049

mg/dscm@7%O2 4.62E-02 3.76E-02 3.77E-02 0.041

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 2.3656 2.3272 2.2 2.298

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 4.19E-04 4.05E-04 3.83E-04 0.000

mg/dscm 5.73E-01 5.78E-01 5.34E-01 0.562

mg/dscm@7%O2 4.86E-01 4.70E-01 4.44E-01 0.467

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0353 0.022 0.0134 0.024

Elb/hr 0.00E+00 0.00E+00 0.00E+00 0.000

lb/mmBtuO2 6.25E-06 3.83E-06 2.33E-06 0.000

mg/dscm 8.55E-03 5.46E-03 3.25E-03 0.006

mg/dscm@7%O2 7.25E-03 4.44E-03 2.71E-03 0.005

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 124.4 139.8 79 114.400

lb/mmBtuO2 7.71E-02 8.56E-02 4.91E-02 0.071

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 31.4 39.7 73.1 48.067

lb/mmBtuO2 1.95E-02 2.43E-02 4.54E-02 0.030

Monday, March 07, 2011 Page 14 of 20
Process Run Data

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 19.1 8.3 7.7 11.700

lb/mmBtuO2 1.18E-02 5.08E-03 4.78E-03 0.007

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 1.7 3.5 1.5 2.233

lb/mmBtuO2 1.05E-03 2.14E-03 9.32E-04 0.001

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 145.2 151.6 88.2 128.333

lb/mmBtuO2 9.00E-02 9.28E-02 5.48E-02 0.079

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 93 100.1 5.9 66.333

lb/mmBtuO2 5.76E-02 6.13E-02 3.67E-03 0.041

Monday, March 07, 2011 Page 15 of 20
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input Million Btus/million BTU using O2 0 0

2 Heat Input Million Btus/million BTU using O2 0 0

3 Heat Input Million Btus/million BTU using O2 0 0

1 Average Heat Input 0 MMBtu/hr 0

2 Average Heat Input 0 MMBtu/hr 0

3 Average Heat Input 0 MMBtu/hr 0

1 Steam Output 0 1000 lb steam/hr 0

2 Steam Output 0 1000 lb steam/hr 0

3 Steam Output 0 1000 lb steam/hr 0

1 Synfuel Firing Rate 0 0

2 Synfuel Firing Rate 0 0

3 Synfuel Firing Rate 0 0

1 Petroleum Coke Firing Rate 0 0

2 Petroleum Coke Firing Rate 0 0

3 Petroleum Coke Firing Rate 0 0

1 Coal Gas Firing Rate 0 0

2 Coal Gas Firing Rate 0 0

3 Coal Gas Firing Rate 0 0

1 Fuel Oil Firing Rate 0 0

2 Fuel Oil Firing Rate 0 0

3 Fuel Oil Firing Rate 0 0

1 Flue Gas Flow Rate 0 dscfm 0

1 Pressure Drop Across FGD (if applicable) 0 in H20 0

1 FGD Scrubber Liquor pH 0 pH 0

1 FGD Scrubber Liquor Flow Rate 0 gal/min 0

1 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

1 Flue Gas Oxygen Content 0 % 0

1 Flue Gas Carbon Dioxide Content 0 % 0

1 Flue Gas Moisture Content 0 % 0

1 Flue Gas Sampling Point Temperature 0 Deg F 0

1 Flue Gas Pressure 0 atm 0

1 Standard Pressure 0 atm 0

1 Standard Temperature 0 Deg F 0

Monday, March 07, 2011 Page 16 of 20
APCD Run Data

Process Lab Run Data

1 Unit Gross Electrical Output 0 MW 0

1 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

Target

Value

1 List all emissions control devices in order of 

process flow. Choose from

0 0

1 drop down lists. If not on list add description and 

provide detailed

0 0

1 desription in section 5a. 0 0

Run Name Value UOM Comments

1 See 4b Comments. 0

Monday, March 07, 2011 Page 17 of 20
Sampling / Stack Data Results Detail

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 9/21/2010 9/27/2010 9/28/2010

Run Start Time 10:15:00 AM 10:05:00 AM 10:00:00 AM

Run Finish Time 7:33:00 PM 6:53:00 PM 6:38:00 PM

Net Traversing Points 49 49 49

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.195 0.195 0.195 0.195

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.985 0.985 0.985 0.985

Barometric Pressure, inches of Mercury 29.5 29.5 29.44 29.480

Average Orifice Meter Differential, inches H2O 1.33 1.34 1.39 1.353

Dry Gas Meter Volume Sampled, cubic feet 321.800 319.828 331.970 324.533

Average Dry Gas Meter Temperature, °F 87.79 89.13 92.73 89.883

Dry Gas Meter Volume Sampled, dscf 302.232 299.654 308.416 303.434

Total Moisture Liquid collected, g 912.6 907.7 936.9 919.067

Volume of Water Vapor, standard cubic feet 42.96 42.73 44.10 43.263

Moisture Content of Stack Gas, % 12.45 12.48 12.51 12.480

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8755 0.8752 0.8749 0.875

Carbon Dioxide, % 11.1 13 13.5 12.533

Oxygen, % 6 4.7 4 4.900

Carbon Monoxide & Nitrogen, % 82.9 82.3 82.5 82.567

Fuel Factor 1.34 1.25 1.25

Dry Molecular Weight, lb/lb-Mole 30.02 30.27 30.32 30.203

Wet Molecular weight, lb/lb-Mole 28.52 28.74 28.78 28.680

Flue Gas Static Pressure, inches of H2O 2 2 2.11 2.037

Absolute Flue Gas Pressure, inches of Mercury 29.65 29.65 29.60 29.633

Average Stack Gas Temperature, °F 310.79 304.96 307.13 307.627

Average Velocity Head, inches of H2O 1.5258455698

2608

1.467626907

18753

1.537299817

49811

1.510

Average Stack Gas Velocity, feet/second 84.69 82.43 84.49 83.870

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 100.5 101.7 102.6 101.600

Percent Excess Air, % 37.8 27.6 22.5 29.300

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 18 of 20
Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 9/13/2010 9/14/2010 9/15/2010

Run Start Time 4:00:00 PM 1:05:00 PM 9:55:00 AM

Run Finish Time 8:00:00 PM 5:15:00 PM 2:05:00 PM

Net Traversing Points 25 25 25

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.195 0.195 0.195 0.195

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 1.02 1.02 1.02 1.020

Barometric Pressure, inches of Mercury 29.68 28.75 29.5 29.310

Average Orifice Meter Differential, inches H2O 1.35 1.34 1.36 1.350

Dry Gas Meter Volume Sampled, cubic feet 149.430 149.492 151.554 150.159

Average Dry Gas Meter Temperature, °F 89.44 85.60 94.42 89.820

Dry Gas Meter Volume Sampled, dscf 145.782 142.279 145.644 144.568

Total Moisture Liquid collected, g 440.8 446.4 447.9 445.033

Volume of Water Vapor, standard cubic feet 20.75 21.01 21.08 20.947

Moisture Content of Stack Gas, % 12.46 12.87 12.64 12.657

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8754 0.8713 0.8736 0.873

Carbon Dioxide, % 13.2 13.8 13.4 13.467

Oxygen, % 4.5 3.8 4.2 4.167

Carbon Monoxide & Nitrogen, % 82.3 82.4 82.4 82.367

Fuel Factor 1.24 1.24 1.25

Dry Molecular Weight, lb/lb-Mole 30.29 30.36 30.31 30.320

Wet Molecular weight, lb/lb-Mole 28.76 28.77 28.75 28.760

Flue Gas Static Pressure, inches of H2O 2 2 2.3 2.100

Absolute Flue Gas Pressure, inches of Mercury 29.83 28.90 29.67 29.467

Average Stack Gas Temperature, °F 310.00 309.83 307.83 309.220

Average Velocity Head, inches of H2O 1.5227015826

9525

1.503899564

08329

1.505156126

04677

1.511

Average Stack Gas Velocity, feet/second 83.95 84.74 83.59 84.093

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 97.2 97.4 97.9 97.500

Percent Excess Air, % 26.1 21.2 23.9 23.733

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 19 of 20
Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 9/13/2010 9/14/2010 9/15/2010

Run Start Time 10:20:00 AM 1:00:00 PM 9:56:00 AM

Run Finish Time 4:41:30 PM 4:09:00 PM 1:00:00 PM

Net Traversing Points 24 24 28

Net Run Time, minutes 122.25 118.25 117.25

Nozzle Diameter, inches 0.143 0.143 0.143 0.143

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.985 0.985 0.985 0.985

Barometric Pressure, inches of Mercury 29.4 29.72 29.68 29.600

Average Orifice Meter Differential, inches H2O 0.41 0.38 0.39 0.393

Dry Gas Meter Volume Sampled, cubic feet 44.789 42.716 43.245 43.583

Average Dry Gas Meter Temperature, °F 90.08 86.17 97.00 91.083

Dry Gas Meter Volume Sampled, dscf 41.653 40.442 40.093 40.729

Total Moisture Liquid collected, g 128.9 120.2 120.7 123.267

Volume of Water Vapor, standard cubic feet 6.07 5.66 5.68 5.803

Moisture Content of Stack Gas, % 12.72 12.28 12.41 12.470

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8728 0.8772 0.8759 0.875

Carbon Dioxide, % 13.2 13.7 13.7 13.533

Oxygen, % 4.5 3.8 3.9 4.067

Carbon Monoxide & Nitrogen, % 82.3 82.5 82.4 82.400

Fuel Factor 1.24 1.25 1.24

Dry Molecular Weight, lb/lb-Mole 30.29 30.34 30.35 30.327

Wet Molecular weight, lb/lb-Mole 28.73 28.82 28.82 28.790

Flue Gas Static Pressure, inches of H2O 2.2 2 2.3 2.167

Absolute Flue Gas Pressure, inches of Mercury 29.56 29.87 29.85 29.760

Average Stack Gas Temperature, °F 310.92 312.83 308.79 310.847

Average Velocity Head, inches of H2O 1.6526769253

6664

1.537172487

52599

1.530632710

99251

1.573

Average Stack Gas Velocity, feet/second 87.96 84.36 83.99 85.437

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 98.0 101.3 101.4 100.233

Percent Excess Air, % 26.1 21.1 21.8 23.000

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 20 of 20