10104 Federal Register / Vol. 89, No. 30 / Tuesday, February 13, 2024 / Notices 

machines shall have instantaneous trip 

units calibrated to trip at 2,500 amperes. 

The trip setting of these circuit breakers 

shall be sealed or locked so that the 

setting cannot be changed. The circuit 

breakers shall have permanent legible 

labels displaying the maximum short 

circuit setting. Calibration, sealing, and 

labeling of circuit breakers shall be 

performed by the circuit breaker 

manufacturer, or an authorized repair 

facility outfitted with calibrated test 

equipment. Each label shall identify the 

circuit breaker as being suitable for 

protecting the No. 4 cables. The labels 

shall be maintained as legible. 

(c) Replacement instantaneous trip 

units used to protect the No. 4 trailing 

cables shall be calibrated to trip at 2,500 

amperes and this setting shall be sealed 

or locked. Calibration, sealing, and 

labeling of the replacement units shall 

be conducted by the device 

manufacturer, or an authorized repair 

facility outfitted with calibrated test 

equipment. 

(d) All circuit breakers used to protect 

the No. 2 trailing cables exceeding 850 

feet in length for the shuttle cars shall 

have instantaneous trip units calibrated 

to trip at 1,500 amperes. The trip setting 

of these circuit breakers shall be sealed 

or locked so that the setting cannot be 

changed. The circuit breakers shall have 

permanent legible labels displaying the 

maximum short circuit setting. 

Calibration, sealing, and labeling of 

circuit breakers shall be performed by 

the circuit breaker manufacturer, or an 

authorized repair facility outfitted with 

calibrated test equipment. Each label 

shall identify the circuit breaker as 

being suitable for protecting the No. 2 

cables. The labels shall be maintained as 

legible. 

(e) Replacement instantaneous trip 

units used to protect the No. 2 trailing 

cables shall be calibrated to trip at 1,500 

amperes and this setting shall be sealed 

or locked. Calibration, sealing, and 

labeling of the replacement units shall 

be conducted by the device 

manufacturer, or an authorized repair 

facility outfitted with calibrated test 

equipment. 

(f) All components that provide shortcircuit protection shall have a sufficient 

interruption rating in accordance with 

the maximum calculated fault current 

available. 

(g) The trailing cables for the mobile 

roof support machines and shuttle cars 

shall be protected by being hung on 

well-installed insulated hangers from 

the section transformer to the slack pile 

of the trailing cable for each machine or 

to the last open crosscut, whichever is 

further outby. 

(h) Prior to putting the mobile roof 

support machines and shuttle cars in 

service for each shift, examinations by 

persons designated by the mine operator 

shall be made to visually examine the 

trailing cables to ensure that the cables 

are in safe operating condition. The 

instantaneous settings of the specially 

calibrated circuit breakers shall also be 

visually examined to ensure that the 

seals or locks have not been removed 

and that they do not exceed the settings 

stipulated in items (b) and (d). 

(i) Permanent warning labels shall be 

installed and maintained on the cover(s) 

of each circuit breaker and the trailing 

cable disconnecting device indicating 

that the cable can only be connected to 

a circuit breaker that is set to trip at its 

pre-determined instantaneous value. 

These labels shall warn miners not to 

change or alter these sealed short-circuit 

settings and warn them not to connect 

the trailing cable to an improperly 

adjusted circuit breaker. 

(j) Any trailing cable that is not in safe 

operating condition or damaged in any 

way shall be removed from service 

immediately and repaired or replaced. 

Each splice or repair in the trailing 

cables shall be made in a workmanlike 

manner and in accordance with the 

instructions of the manufacturer of the 

splice or repair materials. The splice or 

repair shall comply with 30 CFR 75.602 

and 30 CFR 75.604. 

(k) Excessive cable shall be stored 

behind the anchor(s) on equipment that 

use cable reels to prevent cable(s) from 

overheating. Trailing cables anchoring 

points located along haulage roads, belt 

tailpiece, or feeder shall be arranged to 

prevent the shuttle cars from running 

over their trailing cables to minimize 

the need for secondary (temporary) 

trailing cable anchoring points and 

minimize back spooling. 

(l) Before implementation of the terms 

and conditions in MSHA’s Proposed 

Decision and Order (PDO), all miners 

who have been designated to examine 

the integrity of seals or locks and to 

verify the short-circuit settings and 

proper procedures for examining 

trailing cables for defects and damage 

shall receive the training specified in 

item (n). 

(m) Before implementation of the 

terms and conditions in the PDO, the 

circuit breakers outlined above shall be 

inspected by MSHA to ensure their 

conformity with the terms and 

conditions of the PDO. 

(n) Within 60 days after the PDO 

becomes final, the petitioner shall 

submit proposed revisions for its 

approved 30 CFR part 48 training plan 

to the Mine Safety and Health 

Enforcement District Office for the 

District which the mine is located. The 

training shall include the following 

elements: 

(1) Training in the mining methods 

and operating procedures that will 

protect the trailing cables against 

damage; 

(2) Training in proper procedures for 

examining the trailing cables to ensure 

that they are in safe operating condition; 

(3) Training in the hazards of setting 

the short circuit interrupting device(s) 

too high to adequately protect the 

trailing cables; 

(4) Training in how to verify that the 

circuit interrupting device(s) protecting 

the trailing cable(s) are properly set and 

maintained; and 

(5) Training to protect the trailing 

cable(s) against damage caused by 

overheating due to excessive cable 

stored on the cable reel(s) and properly 

adjusting stored cable behind the cable 

anchor(s) as tramming distances change. 

In support of the proposed alternative 

method, the petitioner submitted fault 

analysis for 1,100 feet of the No. 4 and 

No. 2 trailing cables to demonstrate that 

there is enough current available to trip 

the short circuit protection at the time 

of a fault. 

The petitioner asserts that the 

alternate method proposed will at all 

times guarantee no less than the same 

measure of protection afforded the 

miners under the mandatory standard. 

Song-ae Aromie Noe, 

Director, Office of Standards, Regulations, 

and Variances. 

[FR Doc. 2024–02931 Filed 2–12–24; 8:45 am] 

BILLING CODE 4520–43–P 

NATIONAL AERONAUTICS AND 

SPACE ADMINISTRATION 

[Notice: (24–008)] 

Heliophysics Advisory Committee; 

Space Weather Council; Meeting 

AGENCY: National Aeronautics and 

Space Administration. 

ACTION: Notice of meeting. 

SUMMARY: In accordance with the 

Federal Advisory Committee Act, the 

National Aeronautics and Space 

Administration (NASA) announces a 

meeting of the Space Weather Council 

(SWC). The SWC is a subcommittee of 

the Heliophysics Advisory Committee, 

which functions in an advisory capacity 

to the Director, Heliophysics Division, 

in the NASA Science Mission 

Directorate. The meeting will be held for 

the purpose of soliciting, from the 

science community and other persons, 

scientific and technical information 

relevant to program planning. 


lotter on DSK11XQN23PROD with NOTICES1
Federal Register / Vol. 89, No. 30 / Tuesday, February 13, 2024 / Notices 10105 

DATES: Thursday, February 22, 2024, 9 

a.m.–5 p.m.; and Friday, February 23, 

2024, 9 a.m.–5 p.m. eastern time. 

ADDRESSES: Meeting will be virtual. See 

Webex and dial-in information below. 

FOR FURTHER INFORMATION CONTACT: Mrs. 

Karshelia Kinard, Science Mission 

Directorate, NASA Headquarters, 

Washington, DC 20546, (202) 358–2355 

or karshelia.kinard@nasa.gov. 

SUPPLEMENTARY INFORMATION: This 

meeting will only be available by Webex 

or dial-in for members of the public. 

Any interested person may join via 

Webex at https://nasaenterprise

.webex.com, the meeting number is 

2761 312 2137, and the password is 

SWCWinter2024! (case sensitive), both 

days. To join by dial-in telephone call, 

use US Toll +1–415–527–5035 (Access 

code: 2761 312 2137), both days, to 

participate in this meeting. 

The agenda for the meeting includes 

the following topics: 

• Discussion of Space Weather Council 

future advisory topics and activities 

such as: 

Æ Coordination of Space Weather 

Council with Other Space Weather 

Groups 

Æ Space Weather Science and 

Modeling Gap Analysis 

Æ Space Weather and Deep Space 

Exploration 

Æ Research to Operations to Research 

Process 

Patricia Rausch, 

Advisory Committee Management Officer, 

National Aeronautics and Space 

Administration. 

[FR Doc. 2024–02869 Filed 2–12–24; 8:45 am] 

BILLING CODE P 

NATIONAL CREDIT UNION 

ADMINISTRATION 

Sunshine Act Meetings 

TIME AND DATE: 10 a.m., Thursday, 

February 15, 2024. 

PLACE: Board Room, 7th Floor, Room 

7B, 1775 Duke Street (All visitors must 

use Diagonal Road Entrance) 

Alexandria, VA 22314–3428. 

STATUS: Open. 

MATTERS TO BE CONSIDERED: 

1. Board Briefing, Share Insurance 

Fund Quarterly Report. 

2. Final Interpretive Ruling and Policy 

Statement, Minority Depository 

Institution Preservation Program. 

CONTACT PERSON FOR MORE INFORMATION: 

Melane Conyers-Ausbrooks, Secretary of 

the Board, Telephone: 703–518–6304. 

Melane Conyers-Ausbrooks, 

Secretary of the Board. 

[FR Doc. 2024–02994 Filed 2–9–24; 11:15 am] 

BILLING CODE 7535–01–P 

NUCLEAR REGULATORY 

COMMISSION 

[NRC–2022–0224] 

Information Collection: Identity, 

Credential, and Access Management 

System 

AGENCY: Nuclear Regulatory 

Commission. 

ACTION: Proposed information 

collection; request for comment. 

SUMMARY: The U.S. Nuclear Regulatory 

Commission (NRC) invites public 

comment on this proposed information 

collection. The information collection is 

entitled, ‘‘Identity, Credential, and 

Access Management System.’’ 

DATES: Submit comments by April 15, 

2024. Comments received after this date 

will be considered if it is practical to do 

so, but the Commission is able to ensure 

consideration only for comments 

received on or before this date. 

ADDRESSES: You may submit comments 

by any of the following methods; 

however, the NRC encourages electronic 

comment submission through the 

Federal rulemaking website: 

• Federal rulemaking website: Go to 

https://www.regulations.gov and search 

for Docket ID NRC–2022–0224. Address 

questions about Docket IDs in 

Regulations.gov to Stacy Schumann; 

telephone: 301–415–0624; email: 

Stacy.Schumann@nrc.gov. For technical 

questions, contact the individual listed 

in the FOR FURTHER INFORMATION

CONTACT section of this document. 

• Mail comments to: David C. 

Cullison, Office of the Chief Information 

Officer, Mail Stop: T–6 A10M, U.S. 

Nuclear Regulatory Commission, 

Washington, DC 20555–0001. 

For additional direction on obtaining 

information and submitting comments, 

see ‘‘Obtaining Information and 

Submitting Comments’’ in the 

SUPPLEMENTARY INFORMATION section of 

this document. 

FOR FURTHER INFORMATION CONTACT: 

David Cullison, Office of the Chief 

Information Officer, U.S. Nuclear 

Regulatory Commission, Washington, 

DC 20555–0001; telephone: 301–415– 

2084; email: Infocollects.Resource@

nrc.gov. 

SUPPLEMENTARY INFORMATION: 

I. Obtaining Information and 

Submitting Comments 

A. Obtaining Information 

Please refer to Docket ID NRC–2022– 

0224 when contacting the NRC about 

the availability of information for this 

action. You may obtain publicly 

available information related to this 

action by any of the following methods: 

• Federal Rulemaking Website: Go to 

https://www.regulations.gov and search 

for Docket ID NRC–2022–0224. A copy 

of the collection of information and 

related instructions may be obtained 

without charge by accessing Docket ID 

NRC–2022–0224 on this website. 

• NRC’s Agencywide Documents 

Access and Management System 

(ADAMS): You may obtain publicly 

available documents online in the 

ADAMS Public Documents collection at 

https://www.nrc.gov/reading-rm/ 

adams.html. To begin the search, select 

‘‘Begin Web-based ADAMS Search.’’ For 

problems with ADAMS, please contact 

the NRC’s Public Document Room (PDR) 

reference staff at 1–800–397–4209, at 

301–415–4737, or by email to 

PDR.Resource@nrc.gov. A copy of the 

collection of information and related 

instructions may be obtained without 

charge by accessing ADAMS Accession 

No. ML23325A121. The supporting 

statement and guidance document are 

available in ADAMS under Accession 

Nos. ML23206A192 and ML23331A942. 

• NRC’s PDR: The PDR, where you 

may examine and order copies of 

publicly available documents, is open 

by appointment. To make an 

appointment to visit the PDR, please 

send an email to PDR.Resource@nrc.gov 

or call 1–800–397–4209 or 301–415– 

4737, between 8 a.m. and 4 p.m. eastern 

time (ET), Monday through Friday, 

except Federal holidays. 

• NRC’s Clearance Officer: A copy of 

the collection of information and related 

instructions may be obtained without 

charge by contacting the NRC’s 

Clearance Officer, David C. Cullison, 

Office of the Chief Information Officer, 

U.S. Nuclear Regulatory Commission, 

Washington, DC 20555–0001; telephone: 

301–415–2084; email: 

Infocollects.Resource@nrc.gov. 

B. Submitting Comments 

The NRC encourages electronic 

comment submission through the 

Federal rulemaking website (https://

www.regulations.gov). Please include 

Docket ID NRC–2022–0224, in your 

comment submission. 

The NRC cautions you not to include 

identifying or contact information in 


lotter on DSK11XQN23PROD with NOTICES1