TECHNICAL PUBLICATION

Reducing NOX Emissions and Commissioning Time

on Southern Company Coal Fired Boilers

With Low NOX Burners and CFD Analysis

by

Bonnie Courtemanche, P.E.

Darrell Dorman

Ali Yilmaz, Ph.D.

Riley Power Inc.

(Formerly Babcock Borsig Power, Inc.)

Worcester, Massachusetts

and

Lee Esclavon, P.E.

Southern Company

Atlanta, Georgia

Presented at

Electric Power 2003

March 4-6, 2003

Houston, Texas

and

28th International Technical Conference on Coal Utilization & Fuel Systems

March 10-13, 2003

Clearwater, Florida

and

Combined Power Plant Air Pollution Control Mega Symposium

May 19-22

Washington, DC

Riley Power Inc.

5 Neponset Street

Worcester, Massachusetts 01606

www.babcockpower.com

T-182
®Riley Power Inc. 2003

REDUCING NOx EMISSIONS AND COMISSIONING TIME 

ON SOUTHERN COMPANY COAL FIRED BOILERS 

WITH LOW NOx BURNERS AND CFD ANALYSIS

by

Bonnie Courtemanche, PE

Darrell Dorman

Ali Yilmaz, PhD

Riley Power Inc., Worcester, Massachusetts

(Formerly Babcock Borsig Power, Inc.)

and

Lee Esclavon, PE

Southern Company

Atlanta, Georgia

ABSTRACT

Riley Power Inc. (RPI), a subsidiary of Babcock Power Inc. has successfully retrofitted two

different types of Southern Company utility boilers with low NOx dual air zone burners. The first

type is a 115 MWg, front wall fired, sub-critical boiler while the second type is a 535 MWg, twohigh-cell opposed-fired, supercritical boiler. The low NOx burners in both boiler types feature

CCV® coal nozzles and low swirl coal spreaders in conjunction with the latest flame stabilizer

ring technology which provides enhanced NOx reduction. The objective of these projects was to

reduce NOx emissions significantly without the use of overfire air (OFA) or burner re-spacing

while firing a wide variety of eastern bituminous coals and maintaining boiler performance as

determined during pre-retrofit operation. To minimize startup, commissioning and optimizing

time (and costs), computational fluid dynamics (CFD) modeling was used to determine initial low

NOx burner settings for optimum NOx performance.

Performance guarantees for NOx emissions, CO emissions, and unburned carbon (UBC) in fly

ash along with reheat temperature, superheat steam temperature and boiler efficiency were all

achieved. For both boiler types, the NOx emissions were reduced more than 60% from uncontrolled levels using a “burners only” approach. These two boilers, with different designs and firing arrangements, represent some of the lowest NOx levels achieved in the industry without the

need for OFA. Commissioning of the burners was reduced from a typical low NOx burner installation by approximately 50 percent. This paper describes the results from these low NOx burner

retrofit projects including boiler performance data prior to installation of burners and post-retrofit data after installation of the low NOx burners.

INTRODUCTION

RPI developed the Combustion Controlled Venturi (CCV®) burner in the early 1980s to lower

NOx emissions from pulverized coal fired utility boilers. The CCV® burner design has evolved

throughout the years, and the latest Dual Air Zone CCV® Burner is capable of achieving significant NOx reductions in various types of applications, new and retrofit1. To date, RPI has pro-
2

vided over 1,800 low NOx CCV® Burners to the power industry with a total electric generating

capacity of nearly 22,000 MW.

Figure 1 shows the latest Dual Air Zone CCV® burner design for reducing NOx emissions

from fossil-fired utility and industrial boilers. Pulverized coal is the primary fuel burned using

this design. However, with the proper equipment installed for dual fuel firing capability, oil

and/or natural gas can also be fired. The patented venturi coal nozzle, low swirl coal spreader,

and flame stabilizer ring in the Dual Air Zone CCV® burner results in a well attached fuel rich

flame core, the fundamental condition necessary for minimizing the formation of both fuel and

thermal NOx.

Figure 1 Typical low NOx Dual Air Zone Burner

Total combustion air flow to the Dual Air Zone CCV® burner is controlled by an automated

air shroud that surrounds the burner air register. The air entering the register is divided into secondary air (SA) and tertiary air (TA) streams by a manual SA flow control damper. The register

also features fixed SA swirl vanes and manually adjustable TA swirl vanes. The register design

provides independent control of total air flow, SA/TA flow split, and TA swirl. The burner air

flow is measured using individual burner air flow probes, supplied by Air Monitor Corporation,

for secondary and tertiary air2. The ability to control internal burner air staging with the Dual Air

Zone CCV® burner makes it possible to control NOx formation rate.

Start-up and optimization of any low NOx burner retrofit can be time consuming and can

involve many adjustments. To minimize this process RPI utilized Computational Fluid Dynamics

(CFD) to model the CCV® Dual Air Zone burner. These models greatly improve RPI’s ability to

initially adjust the burners to provide proper swirl and air flow splits, thereby decreasing the

amount of time required for parametric testing. RPI’s low NOx burner design utilizes Air Monitor

Corporation’s Individual Burner Air Measurement (IBAMTM) probes to measure the air flows in

the secondary and tertiary air passages2. The combination of these systems allowed for the startup and optimization of the low NOx burners to be completed in relatively short time duration.
3

As a result of the State of Georgia’s efforts to reduce ozone in the Atlanta ozone nonattainement area, Georgia Power (a subsidiary of Southern Company) is required to make significant

reductions in NOx emissions during the ozone season (May-September, beginning in 2003) from

seven plants in the northern part of Georgia. RPI was contracted by Southern Company to retrofit Hammond Units 1, 2 and 3, and Branch Units 3 and 4 with low NOx Dual Air Zone CCV®

coal burners. The Hammond units feature a front wall fired furnace while the Branch units feature an opposed cell-fired furnace. To date, burner performance optimization and acceptance tests

have been successfully completed on Hammond Units 1 and 2 and Branch 4 with all performance

guarantees being met. This paper presents results of burner performance tests at these Georgia

Power plants along with technical details of the project. The use of CFD modeling on both of

these low NOx burner retrofit projects is described in detail, presenting the benefits of CFD modeling with examples.

HAMMOND UNITS 1, 2, and 3

Background

Hammond Units 1, 2, and 3 are identical 115 MWg Babcock & Wilcox (B&W) sub-critical

boilers that went into service in the 1950’s. The key design features of these units are provided

in Table 1. A side cross section of the units is shown in Figure 2. Southern Company test crews

conducted baseline emissions and boiler performance tests in June 2000.

Unit rating: 115 MWg

Main steam flow @ MCR: 725,000 lb/hr

Reheat steam flow @ MCR: 650,000 lb/hr

Design steam temperature superheat/reheat: 1005°F / 1005°F

Furnace draft: balanced

Furnace dimensions: 34 ft wide x 21 ft deep

Burner firing arrangement: front wall, 4 wide x 4 high

Pulverizers: 4 B&W EL

Burner capacity @ peak load (122% MCR): 72 MMBtu/hr

Table 1 Hammond Units 1, 2, and 3 unit configuration

Figure 2 Hammond units 1, 2, and 3 schematic
4

Retrofit Goals and Scope

RPI was contracted in December 2000 to retrofit Hammond Unit 2 followed by Units 1 and

3. The retrofit goals were to reduce NOx to ≤ 0.38 lb/MMBtu with acceptable levels of CO

and unburned carbon (UBC) in the fly ash while maintaining acceptable boiler performance.

The design coal analysis is provided in Table 2. The major equipment in RPI’s retrofit package included: 

• Sixteen low NOx CCV® Dual Air Zone burners with venturi nozzle, low swirl coal spreader and flame stabilizer ring,

• Sixteen new retractable class I oil ignitors, and

• Thirty-two new flame scanners. 

Proximate (wt %) Ultimate (wt %)

Fixed Carbon 54.74 Carbon 75.49

Volatile 32.38 Hydrogen 4.50

Moisture 5.45 Nitrogen 1.39

Ash 7.43 Oxygen 4.62

Sulfur 0.77

FC/VM Ratio

HHV (Btu/lb)

1.53

13,364

Moisture

Ash

5.45

7.43

Table 2 Design coal analysis (as received basis), Hammond units

Hammond Unit 2 Post-retrofit Experience and Burner Performance Test Results

The unit outage occurred during the fall of 2001 with initial operation beginning in December

2001. Optimization tests scheduled for January 2002 were interrupted for an eight-week turbine

outage. In April 2002 RPI and Southern Company test crews completed the unit optimization and

acceptance testing. Additional system problems were encountered during the burner commissioning period. These additional system problems stem from the Distributed Control System

(DCS) retrofit, ignitor control system problems, scanner setup problems, turbine vibration, and

questions about the primary air flow measurement issues.

During the initial optimization in January 2002, the unit demonstrated difficulty maintaining

scannable and stable coal flames at 33% unit load with only two mills in service. During the

eight-week turbine outage RPI and Southern Company analyzed the most recent mill and unit

data to determine the cause of the low load flame stability problems. CFD modeling results suggested that primary air to coal ratios greater than 3.0 could produce detached flames. In April

2002 following the turbine outage, mill primary air characterization tests were conducted to confirm whether or not excessive primary air to coal ratio was the root cause as initially surmised.

Mill 2D was found to have a higher actual primary air flow than indicated in the control room.

The higher air flow caused the air to coal ratio to exceed the design limits of the new burners.

The air flow curves were adjusted in the DCS for Mill 2D so that the DCS values matched the

actual as measured values.

Subsequent low load tests at 33% MCR again resulted in detached coal flames and also pulverizer trips. Following additional investigation using the IBAMTM probes and CFD model, it

was determined that the flame stability problems resulted from inadequate air flow through the in

service burners. In service burner air flow was masked by a combination of backend in-leakage

and excessive air flow through out of service burners. Burner air shroud opening on out of service burners was reduced, and unit excess air level was increased resulting in well-attached and
5

stable coal flames. After adjustment of the mill and correction to the unit air flow at low load was

completed, optimization testing was resumed.

Substantial air mal-distribution was discovered in the burner windbox as evidenced by CO

spikes measured at the economizer outlet gas-sampling grid. Burner air shrouds were biased as

necessary and peak CO levels were reduced from 3000+ ppm to 60 ppm. Full load tests were

conducted at various TA swirl settings to confirm the CFD modeling results. Only four of sixteen

burners required settings slightly different than the CFD modeling predicted. 

Acceptance tests were conducted at three boiler load points as contractually mandated. A comparison of baseline, guarantee, and post-retrofit data for NOx and fly ash UBC is provided in

Figures 3 and 4. As the data indicate, the NOx levels were consistently lower than the guarantee

of 0.38 lb/MMBtu at all loads. The actual NOx attained was approximately 0.36 lb/MMBtu,

which represents some of the lowest NOx emissions for a “burners only” approach on this type

of boiler firing eastern bituminous coal. Typical CO emissions ranged between 30 to 39 ppm for

the entire load range tested.

Figure 3 Comparison of pre-retrofit, guaranteed, and post-retrofit NOx emissions

Figure 4 Comparison of pre-retrofit, guaranteed, and post-retrofit flyash UBC

Pre-Retrofit

Guaranteed

Post-Retrofit

Boiler Load (% MCR)

25 35 45 55 65 75 85 95 105 115 125

35

30

25

20

15

10

5

0

Flyash UBC (%)

22.0 22.0

22.0

11.4

6.0

10.1

8.1

11.8

14.5

Pre-Retrofit

Guaranteed

Post-Retrofit

Boiler Load (% MCR)

NOx @ Economizer Outlet (lb/MMBtu)

25 35 45 55 65 75 85 95 105 115 125

1.0

0.9

0.8

0.7

0.6

0.5

0.4

0.3

.590

.760

.890

.380 .380 .380

.350 .356 .360
6

In addition to these measurable guarantees, the Dual Air Zone CCV® burners retrofitted on

this unit were able to maintain stable, attached flames with a flame length that fit into a relatively shallow furnace depth of 21 feet. Typically for a shallow furnace and a burner heat input of 72

MMBtu/hr the flame length is a concern because of water wall wastage due to flame impingement. The RPI patented low NOx coal burner design makes it possible to control the flame length

on relatively shallow units. The flame length was also carefully analyzed during the design phase.

A RPI calculation method is used in conjunction with the spreader angle selection. These calculations were compared to the furnace depth to verify the flames would not impinge on the rear

wall.

Hammond Units 1 and 3 were retrofitted with identical equipment and restarted in October and

December 2002, respectively. Test result for Unit 1 was very similar to the results on Unit 2 with

all emissions and performance guarantees being met. Commissioning time was approximately 10

days for Unit 1. At the time of writing, performance testing on Unit 3 is currently in progress.

BRANCH UNITS 3 and 4

Background

Georgia Power Harllee Branch Units 3 and 4 are 535 MWg, supercritical Babcock & Wilcox

cell fired boilers that went into initial operation in the late 1960’s. The key design features of

these units are provided in Table 3. A side cross section of the units is shown in Figure 5.

Southern Company test crews conducted baseline emissions and boiler performance tests in the

spring of 2000.

Unit rating: 535 MWg

Main steam flow @ MCR: 3,569,700 lb/hr

Reheat steam flow @ MCR: 3,057,900 lb/hr

Design steam temperature superheat/reheat: 1000°F / 1000°F

Furnace draft: balanced draft

Furnace dimensions: 54 ft wide x 42 ft deep

Burner firing arrangement: (20) 2-high cell opposed wall, 5 wide x 2 high

Pulverizers: (10) B&W EL-76

Burner capacity @ peak load (103% MCR): 116 MMBtu/hr

Table 3 Branch 3 and 4 unit configurations

Figure 5 Branch Units 3 and 4 schematic
7

Retrofit Goals and Scope

RPI was contracted in July 2001 to retrofit Branch Units 3 and 4 starting with Unit 4 and followed by Unit 3. The major low NOx retrofit project goals established by Georgia Power were

to lower NOx to ≤ 0.45 lb/MMBtu with acceptable levels for CO and fly ash unburned carbon,

while maintaining acceptable boiler performance. The design coal analysis is shown in Table 4.

The major retrofit equipment for each unit included the following:

• Forty low NOx Dual Air Zone CCV® burners with venturi nozzle, low swirl coal spreader

and flame stabilizer ring,

• Forty new retractable, class I, oil fired ignitors mounted in the secondary air annulus of each

burner, and

• Forty new flame scanners. 

Proximate (wt %) Ultimate (wt %)

Fixed Carbon 50.57 Carbon 71.09

Volatile 34.38 Hydrogen 4.73

Moisture 6.00 Nitrogen 1.59

Ash 9.00 Oxygen 6.23

Sulfur 1.31

FC/VM Ratio 1.47 Moisture 6.00

AFT (°F) 2,622 Ash 9.00

HHV (Btu/lb) 12,550

Table 4 Design coal analysis (as received basis), Branch units

RPI’s retrofit solution consisted of a “burners only” approach. Overfire air (OFA) ports, as

proposed by other low NOx burner suppliers, were not utilized to preclude staged combustion and

the subsequent concern for lower furnace corrosion. The existing cell burner configuration was

also retained without the need to re-space the burners into a typical wall fired arrangement. CFD

modeling by the ignitor vendor demonstrated the need for individual ignitors for each burner due

to the inherent differences in flame shape between the low NOx Dual Air Zone CCV® burner

with low swirl coal spreader and the original B&W cell burner with diverging impeller.

CFD aerodynamic modeling was used to determine the initial Dual Air Zone CCV® burner

register settings for SA/TA flow split and TA swirl as discussed in the “Single Burner CFD

Modeling” section of this paper.

Branch 4 Burner Performance Test Results

Unit 4 was restarted the last week of February 2002 following a six-week outage. Pre-optimization tests were conducted to balance oxygen levels across the economizer outlet gas sampling grid using the burner air shrouds. A total of four optimization tests were conducted between

March 8 and 11 at the corresponding steam flows for peak, intermediate, and low loads per contract requirements. A single optimization test was conducted on March 22 at full load. Final

acceptance tests were conducted on March 27 and 28 by Southern Company test crews and all

performance guarantees were demonstrated. A comparison of the baseline, guarantee, and postretrofit acceptance test results for NOx, CO, and flyash UBC is provided in Figures 6 through 8.

The only burner adjustments made during optimization testing were individual burner air

shroud settings that were biased to balance oxygen and minimize CO at the economizer outlet gas

sampling grid. The burner register settings for SA/TA flow split and TA swirl determined by CFD

modeling were used throughout the optimization and acceptance tests, thus minimizing the time

required for burner optimization and tuning.
8

1.20

1.00

0.80

0.60

0.40

0.20

0.00

0 20 40 60 80 100 120

Pre-Retrofit

Guaranteed

Post-Retrofit

Boiler Load (% MCR)

NOx @ Economizer Outlet (lb/MMBtu)

0.68

0.72

1.10

0.45 0.45 0.45

0.34 0.33

0.43

0 20 40 60 80 100 120

Boiler Load (% MCR)

Pre-Retrofit

Guaranteed

Post-Retrofit

50

40

30

20

10

0

CO @ Economizer Outlet (ppmdv)

51 51 51

6

3

6

0 0 0

0 20 40 60 80 100 120

Boiler Load (% MCR)

Pre-Retrofit

Guaranteed

Post-Retrofit

0

7.0

6.0

5.0

4.0

3.0

2.0

1.0

Flyash UBC (%)

3.7

4.6

5.7

3.2

2.8

5.3

1.1

1.9

2.6

Figure 6 Comparison of pre-retrofit, guarantee, and post-retrofit NOx

Figure 7 Comparison of pre-retrofit, guarantee, and post-retrofit CO

Figure 8 Comparison of pre-retrofit, guarantee, and post-retrofit flyash UBC
9

At the time of writing, fabrication is complete for the Branch Unit 3 equipment. The outage

is currently scheduled to begin March 1, 2003 with a tentative restart the end of April 2003. 

SINGLE BURNER CFD MODELING

CFD modeling adds value to the burner design phase of a low NOx retrofit project. Plug-in

low NOx burner retrofits require proper control settings to meet boiler performance guarantees.

Typically in retrofit projects, boiler performance guarantees require maintaining pre-retrofit boiler efficiency, superheat and reheat steam temperatures, and windbox-to-furnace pressure differentials while meeting guarantee NOx emissions, CO emissions, and flyash UBC values. Simple

2-D single burner CFD models employing only aerodynamics and/or combustion become a costeffective design tool to predict burner settings necessary to achieve optimum near burner aerodynamics for low NOx emissions and low UBC as well as estimated changes in flame length and

attachment. The CFD results highlight the type and location of the flame structure’s internal recirculation zone (IRZ). Aerodynamic interactions of swirling air flows leaving the burner dominate the control of IRZ characteristics. Near burner aerodynamics relate qualitatively to flame

behavior (e.g., flame length and attachment), UBC and NOx emissions when coupled with fullscale burner combustion test results.

Figure 9 shows the predicted near burner internal re-circulation zone (IRZ) for the Hammond

Unit 2 low NOx Dual Air Zone CCV® coal burner at three different tertiary air (TA) swirl vane

settings. The computed stream-lines for low TA swirl angle indicate that two near burner flow reFigure 9 Comparison of CFD predictions of near burner flow behavior and actual burner 

performance test data of UBC and NOx emissions for Hammond Unit 2

TA Vane Angle UBC NOx

(Degrees) (%) (lb/MMBtu)

30 7.89 0.397

40 13.33 0.368

35 8.48 0.354
10

Figure 10 Effect of SA/TA flow rate ratio on near burner aerodynamics at Hammond Unit 2

(SA/TA ratio= (a) 0.72x, (b) 0.90x, (c) x, and (d) 1.15x, 

x being the optimum setting for NOx and flyash UBC)

circulation zones exist: a) an external re-circulation zone (ERZ) driven by secondary air (SA) and

b) an IRZ driven partially by primary air (PA). The PA-driven IRZ is essential for establishing a

fuel rich zone during the initial combustion process, good flame attachment, and low flyash UBC.

Figure 9 indicates that the PA-driven IRZ diminishes as TA swirl vane angle increases, resulting

in less coal particle capture by the IRZ and increased flyash UBC levels. To the right of the CFD

results in Figure 9 are actual burner optimization test data on flyash UBC and NOx emissions

recorded at Hammond Unit 2. The test data agree well with the indications in the CFD predictions, i.e., UBC is the lowest for a strong PA-driven IRZ at low TA angles while flyash UBC

sharply increases as the PA-driven IRZ disappears at high TA angles.

The effect of internal air staging on near burner aerodynamics is also studied using CFD.

Figure 10 shows the predicted near burner aerodynamics over a range of SA/TA flow rate ratio.

The near burner aerodynamics change as the SA/TA flow rate ratio is increased from cases (a) to

(d) in Figure 10. The cases shown in Figures 11b and 11c provided optimum burner settings for

NOx and flyash UBC at Hammond Unit 2.

Figure 11 compares CFD predicted and actual low NOx coal flames produced by the cell burners at Branch Unit 4. The CFD flame predictions, i.e., temperature contours, compare favorably

with observed flame attachment, shape, and length. For low NOx emissions in a cell-fired burner arrangement, achieving a narrow coal flame with little flame interaction is critical for achieving low NOx emissions. As predicted by CFD modeling and shown in Figure 11, the coal flames

do not interact and thus low NOx is achieved. The pulverized coal fineness level at Branch Unit

4 was below desired levels on 200 Mesh. The average coal fineness was 98.9 % through 50 Mesh,

82.7% through 100 Mesh, and 51% through 200 Mesh. Due to substandard pulverized coal fineness level at Branch 4, the CFD predictions showed a slight flame detachment at the burner discharge. 
11

Figure 11 Comparison of CFD predicted and observed flame conditions at Branch Unit 4

(CFD results indicate predicted temperature contour)

Furnace Type 

Front Wall-Fired 

Subcritical 

(Hammond Unit 2) 

Cell-Fired 

Supercritical 

(Branch Unit 4) 

Number of Burners 16 40 

Data Source CFD 

Results 

Accept 

Test 

CFD 

Results 

Accept 

Test 

SA Damper opening (in.) 1.25 1.25 1.75 1.88 

Avg. Burner Shroud Position (% open) 60 50 60 67 

TA Vane Angle (°) 30-35 35 30 30 

PA Coal Spreader Setback (in.) 1 1 1 1 

dP Windbox-Furnace (iwc) 4.50 4.57 4.00 4.10 

Avg. SA/TA Flow Ratio x 1.16x y 0.92y 

Optimization Test Duration (Days) -- 14 -- 2 

Table 5 Comparison of CFD-recommended burner settings and

finalized burner settings from peak load guarantee testing

CONCLUSIONS

The latest RPI Dual Air Zone CCV® burner design is capable of achieving NOx reductions in

excess of 60% from uncontrolled levels using a “burners only” approach. These NOx reductions

are achieved with minimal impact to CO emissions and flyash UBC as demonstrated at Hammond

Units 1, 2, and 3 and Branch Unit 4. The cell-fired configuration is deemed by the industry as a

potentially difficult low NOx retrofit application due to the very high burner zone heat release

rates and close burner spacing. The ability to achieve substantial NOx reduction on cell fired

units like Branch Unit 4 without OFA or the need for burner re-spacing has been demonstrated

using RPI’s patented low NOx Dual Air Zone CCV® burner technology. 

CFD modeling can also be used to predict burner settings to achieve optimum near burner

aerodynamics. These predictions expedite low NOx burner tuning efforts and boiler commissioning in both new boiler and burner retrofit projects. Table 5 compares burner settings and performance from CFD-derived recommendations and field test results for Hammond Unit 2 and

Branch Unit 4 CCV® Dual Air Zone low NOx coal burner retrofit projects. The field test results

are final burner settings for the performance guarantee tests at peak unit loads. 
12

The low NOx retrofit projects with Southern Company demonstrated that CFD modeling of

Dual Air Zone CCV® burner aerodynamics greatly reduced burner setting and tuning time prior

to the guarantee acceptance tests. The two projects met all the performance guarantees with minimal burner tuning efforts (a 50% reduction in testing and setup time). In these cases the economic value of CFD is obvious and very real. CFD predictions of burner settings for startup can

trim two to three weeks off burner tuning duration and boiler commissioning. Not only do startup and commissioning costs go down many thousands of dollars, but the unit also produces full

power and revenue during what would normally have been a relatively long period for tuning and

testing.

REFERENCES

1. Penterson, C. and Ake, T., “Latest Developments and Application of DB Riley’s Low NOx

CCV® Burner Technology,” Presented at the 23rd International Technical Conference on

Coal Utilization and Fuel Systems, Clearwater, FL, March 1998.

2. A. Yilmaz and D. Paresh, “Individual Burner Air Flow Measurement and CFD Modeling

Expedites Low NOx Burner Optimization and Boiler Commissioning,” Presented at 28th

International Technical Conference on Coal Utilization and Fuel Systems, Clearwater, FL,

March 10-13, 2003.

The data contained herein is solely for your information and is not offered,

or to be construed, as a warranty or contractual responsibility.