Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Monday, March 07, 2011 Page 1 of 18
Facility Information:

PREPA Aguirre Power Station

Enter physical Address

Enter physical city

Contact: Person to contact for more detail

Phone: Of above person

Fax: Of above person

Email: Of above person

Testing Company:

Name of primary testing organization

US postal address of above

US postal address of abov

Contact: Field test leader

Phone: Of above person

Fax: Of above person

Email: Of above person

Air Permit Number:

Enter your facilities ORIS Number here

Permitted Source ID/Name:

SJ8 Enter the Boiler ID of the tested boiler (left)

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

This description should describe the process and associated controls to differentiate this facility from, or document 

similarity with others of same SCC.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: Enter ARS ID FRS #: Enter FRS ID

SCC / Description 10100404 External Combustion Boilers - Electric Generation - Residual Oil - Grade 6 Oil: 

Tangential Firing 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 0 0 0 0 0 0 0 0

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit % H2O Method 1 - 4 3 180 0

Stack Exit Carbon Monoxide Method 10 3 120 0

Stack Exit Formaldehyde Method 0011 3 120 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Monday, March 07, 2011 Page 2 of 18
Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 0

Stack Exit Other PeCDD Method 23 0

Stack Exit Other HxCDD Method 23 0

Stack Exit Other HpCDD Method 23 0

Stack Exit Other TCDF Method 23 0

Stack Exit Other PeCDF Method 23 0

Stack Exit Other HxCDF Method 23 0

Stack Exit Other HpCDF Method 23 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Stack Exit Total PCBs Method 23 3 480 0

Stack Exit Total TEQ Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 120 0

Stack Exit Hydrogen Chloride Method 26 3 180 0

Stack Exit Hydrogen Fluoride Method 26 3 180 0

Stack Exit Hydrogen Chloride Method 26A 3 180 0

Stack Exit Hydrogen Fluoride Method 26A 3 180 0

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Monday, March 07, 2011 Page 3 of 18
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

In this section, identify the promulgation date of any specified test method that you use for determining the 

procedures followed. This field is also used to document any modifications that are necessary to conduct the 

emissions test if they are outside the requirements of the cited method. If this modification was approved verbally by 

a regulatory agency, the name and date of approval should be included. Written formal approval should be attached 

to this file using the "Attach File" button. Test procedures that are different from those published in the Federal 

Register should be attached using the "Attach File" button.

Total PM2.5 OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable Particulate OTM - 27/28 3 240 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Co2 Method 3A CO2 3 120 0

Stack Exit Co2 Method 3A CO2 3 240 0

Stack Exit O2 Method 3A O2 3 240 0

Stack Exit O2 Method 3A O2 3 480 0

Stack Exit Co2 Method 3A CO2 3 480 0

Stack Exit O2 Method 3A O2 3 120 0

Inorganic (Aqueous) 

Condensible Part.

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Organic Condensible 

Particulate

Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Total Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Filterable Particulate Method 5 3 240 0

Filterable Particulate Method 5/OTM-28 3 240 0 Use only for wet 

stacks. Delete 

OTM27/OTM28 test.

Stack Exit

Stack Exit Sulfur Dioxide Method 6C 3 180 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 180 0

Monday, March 07, 2011 Page 4 of 18
Sampling / Stack Data Results Summary

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 12/13/2010 12/14/2010 12/15/2010

Run Start Time 8:45:00 AM 9:45:00 

AM

8:45:00 AM

Run Finish Time 5:15:00 PM 6:15:00 PM 5:15:00 PM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 239.226 234.030 239.226 237.494

Moisture Content of Stack Gas, % 10.45 9.94 10.45 10.280

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.3 10.3 10.3 10.300

Oxygen, % 8.1 8.1 8.1 8.100

Average Stack Gas Temperature, °F 262.29 262.83 262.29 262.470

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 103.3 102.2 103.3 102.933

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 5 of 18
Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 12/16/2010 12/16/2010 2/17/2010

Run Start Time 8:20:00 AM 2:08:00 PM 8:45:00 AM

Run Finish Time 12:50:00 PM 6:38:00 PM 1:15:00 PM

Net Run Time, minutes 240 240 240

Dry Gas Meter Volume Sampled, dscf 121.854 116.797 118.955 119.202

Moisture Content of Stack Gas, % 10.54 10.57 10.36 10.490

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.3 10.6 10.5 10.467

Oxygen, % 8.1 7.7 7.8 7.867

Average Stack Gas Temperature, °F 261.54 261.00 261.08 261.207

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 102.8 102.7 103.2 102.900

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 12/15/2010 12/16/2010 12/16/2010

Run Start Time 12:00:00 AM

Run Finish Time 11:29:00 PM

Net Run Time, minutes 120

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, % 10.2 10.200

Oxygen, % 8.1 8.100

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2 9190 0 0 3,063.333

Fw 10320 0 0 3,440.000

Fc 1420 0 0 473.333

Monday, March 07, 2011 Page 6 of 18
Emissions Summary

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000071 0.0000000043 0.0000000066 0.000

lb/mmBtuO2 9.82E-13 6.08E-13 9.13E-13 0.000

ng/dscm 1.05E-03 6.49E-04 9.74E-04 0.001

ng/dscm@7%O2 1.14E-03 7.05E-04 1.06E-03 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000078 0.0000000028 0.0000000059 0.000

lb/mmBtuO2 1.08E-12 3.96E-13 8.16E-13 0.000

ng/dscm 1.15E-03 4.23E-04 8.71E-04 0.001

ng/dscm@7%O2 1.25E-03 4.59E-04 9.46E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000029 0.0000000024 0.0000000036 0.000

lb/mmBtuO2 4.01E-13 3.39E-13 4.98E-13 0.000

ng/dscm 4.28E-04 3.62E-04 5.32E-04 0.000

ng/dscm@7%O2 4.65E-04 3.93E-04 5.78E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000033 0.0000000025 0.0000000031 0.000

lb/mmBtuO2 4.56E-13 3.53E-13 4.29E-13 0.000

ng/dscm 4.87E-04 3.77E-04 4.58E-04 0.000

ng/dscm@7%O2 5.29E-04 4.09E-04 4.97E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000043 0.0000000031 0.0000000035 0.000

lb/mmBtuO2 5.95E-13 4.38E-13 4.84E-13 0.000

ng/dscm 6.35E-04 4.68E-04 5.17E-04 0.001

ng/dscm@7%O2 6.90E-04 5.08E-04 5.61E-04 0.001

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000024 0.0000000031 0.000

lb/mmBtuO2 4.43E-13 3.39E-13 4.29E-13 0.000

ng/dscm 4.72E-04 3.62E-04 4.58E-04 0.000

ng/dscm@7%O2 5.13E-04 3.93E-04 4.97E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

Monday, March 07, 2011 Page 7 of 18
RunNumber 1 2 3

Mass_mg 0.0000000067 0.0000000027 0.0000000042 0.000

lb/mmBtuO2 9.27E-13 3.82E-13 5.81E-13 0.000

ng/dscm 9.89E-04 4.07E-04 6.20E-04 0.001

ng/dscm@7%O2 1.07E-03 4.42E-04 6.73E-04 0.001

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000035 0.0000000027 0.0000000034 0.000

lb/mmBtuO2 4.84E-13 3.82E-13 4.70E-13 0.000

ng/dscm 5.17E-04 4.07E-04 5.02E-04 0.000

ng/dscm@7%O2 5.61E-04 4.42E-04 5.45E-04 0.001

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000042 0.0000000036 0.0000000035 0.000

lb/mmBtuO2 5.81E-13 5.09E-13 4.84E-13 0.000

ng/dscm 6.20E-04 5.43E-04 5.17E-04 0.001

ng/dscm@7%O2 6.73E-04 5.90E-04 5.61E-04 0.001

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000019 0.0000000032 0.000

lb/mmBtuO2 4.43E-13 2.69E-13 4.43E-13 0.000

ng/dscm 4.72E-04 2.87E-04 4.72E-04 0.000

ng/dscm@7%O2 5.13E-04 3.12E-04 5.13E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000053 0.0000000028 0.0000000028 0.000

lb/mmBtuO2 7.33E-13 3.96E-13 3.87E-13 0.000

ng/dscm 7.83E-04 4.23E-04 4.13E-04 0.001

ng/dscm@7%O2 8.50E-04 4.59E-04 4.48E-04 0.001

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000068 0.0000000098 0.000000007 0.000

lb/mmBtuO2 9.40E-13 1.39E-12 9.68E-13 0.000

ng/dscm 1.00E-03 1.48E-03 1.03E-03 0.001

ng/dscm@7%O2 1.09E-03 1.61E-03 1.12E-03 0.001

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.0000000554 0.0000000535 0.0000000533 0.000

lb/mmBtuO2 7.66E-12 7.56E-12 7.37E-12 0.000

ng/dscm 8.18E-03 8.07E-03 7.87E-03 0.008

ng/dscm@7%O2 8.88E-03 8.76E-03 8.55E-03 0.009

Monday, March 07, 2011 Page 8 of 18
Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.000000163 0.000000121 0.000000118 0.000

lb/mmBtuO2 2.25E-11 1.71E-11 1.63E-11 0.000

ng/dscm 2.41E-02 1.83E-02 1.74E-02 0.020

ng/dscm@7%O2 2.62E-02 1.99E-02 1.89E-02 0.022

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000261 0.0000000211 0.000000008 0.000

lb/mmBtuO2 3.61E-12 2.98E-12 1.11E-12 0.000

ng/dscm 3.85E-03 3.18E-03 1.18E-03 0.003

ng/dscm@7%O2 4.18E-03 3.45E-03 1.28E-03 0.003

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000079 0.0000000077 0.0000000078 0.000

lb/mmBtuO2 1.09E-12 1.09E-12 1.08E-12 0.000

ng/dscm 1.17E-03 1.16E-03 1.15E-03 0.001

ng/dscm@7%O2 1.27E-03 1.26E-03 1.25E-03 0.001

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.000000433 0.000000325 0.000000282 0.000

lb/mmBtuO2 5.99E-11 4.59E-11 3.90E-11 0.000

ng/dscm 6.39E-02 4.90E-02 4.16E-02 0.052

ng/dscm@7%O2 6.94E-02 5.32E-02 4.52E-02 0.056

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000077 0.000000008 0.000000008 0.000

lb/mmBtuO2 1.06E-12 1.13E-12 1.11E-12 0.000

ng/dscm 1.14E-03 1.21E-03 1.18E-03 0.001

ng/dscm@7%O2 1.24E-03 1.31E-03 1.28E-03 0.001

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000073 0.0000000025 0.0000000024 0.000

lb/mmBtuO2 1.01E-12 3.53E-13 3.32E-13 0.000

ng/dscm 1.08E-03 3.77E-04 3.54E-04 0.001

ng/dscm@7%O2 1.17E-03 4.09E-04 3.84E-04 0.001

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000108 0.0000000058 0.000000007 0.000

lb/mmBtuO2 1.49E-12 8.20E-13 9.68E-13 0.000

Monday, March 07, 2011 Page 9 of 18
ng/dscm 1.59E-03 8.75E-04 1.03E-03 0.001

ng/dscm@7%O2 1.73E-03 9.50E-04 1.12E-03 0.001

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000022 0.0000000017 0.0000000022 0.000

lb/mmBtuO2 3.04E-13 2.40E-13 3.04E-13 0.000

ng/dscm 3.25E-04 2.57E-04 3.25E-04 0.000

ng/dscm@7%O2 3.53E-04 2.79E-04 3.53E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000029 0.0000000016 0.0000000017 0.000

lb/mmBtuO2 4.01E-13 2.26E-13 2.35E-13 0.000

ng/dscm 4.28E-04 2.41E-04 2.51E-04 0.000

ng/dscm@7%O2 4.65E-04 2.62E-04 2.73E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.0000000071 0.0000000111 0.0000000087 0.000

lb/mmBtuO2 9.82E-13 1.57E-12 1.20E-12 0.000

ng/dscm 1.05E-03 1.68E-03 1.28E-03 0.001

ng/dscm@7%O2 1.14E-03 1.82E-03 1.39E-03 0.001

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000083 0.0000000093 0.0000000083 0.000

lb/mmBtuO2 1.15E-12 1.31E-12 1.15E-12 0.000

ng/dscm 1.23E-03 1.40E-03 1.23E-03 0.001

ng/dscm@7%O2 1.34E-03 1.52E-03 1.34E-03 0.001

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000000991 0.0000000657 0.0000000412 0.000

lb/mmBtuO2 1.37E-11 9.29E-12 5.70E-12 0.000

ng/dscm 1.46E-02 9.92E-03 6.08E-03 0.010

ng/dscm@7%O2 1.59E-02 1.08E-02 6.60E-03 0.011

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000000073 0.000000011 0.0000000083 0.000

lb/mmBtuO2 1.01E-12 1.55E-12 1.15E-12 0.000

ng/dscm 1.08E-03 1.66E-03 1.23E-03 0.001

ng/dscm@7%O2 1.17E-03 1.80E-03 1.34E-03 0.001

Compound: OCDD

Average

RunNumber 1 2 3

Monday, March 07, 2011 Page 10 of 18
Mass_mg 0.0000000149 0.0000000041 0.0000000122 0.000

lb/mmBtuO2 2.06E-12 5.80E-13 1.69E-12 0.000

ng/dscm 2.20E-03 6.19E-04 1.80E-03 0.002

ng/dscm@7%O2 2.39E-03 6.72E-04 1.95E-03 0.002

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000089 0.0000000033 0.0000000039 0.000

lb/mmBtuO2 1.23E-12 4.66E-13 5.39E-13 0.000

ng/dscm 1.31E-03 4.98E-04 5.76E-04 0.001

ng/dscm@7%O2 1.42E-03 5.41E-04 6.26E-04 0.001

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000076 0.0000000039 0.0000000066 0.000

lb/mmBtuO2 1.05E-12 5.51E-13 9.13E-13 0.000

ng/dscm 1.12E-03 5.89E-04 9.74E-04 0.001

ng/dscm@7%O2 1.22E-03 6.40E-04 1.06E-03 0.001

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000065 0 0.0000000081 0.000

lb/mmBtuO2 8.99E-13 0.00E+00 1.12E-12 0.000

ng/dscm 9.60E-04 0.00E+00 1.20E-03 0.001

ng/dscm@7%O2 1.04E-03 0.00E+00 1.30E-03 0.001

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000009 0.0000000047 0.0000000066 0.000

lb/mmBtuO2 1.24E-12 6.64E-13 9.13E-13 0.000

ng/dscm 1.33E-03 7.09E-04 9.74E-04 0.001

ng/dscm@7%O2 1.44E-03 7.70E-04 1.06E-03 0.001

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm 0.00E+00 0.00E+00 0.00E+00 0.000

ng/dscm@7%O2 0.00E+00 0.00E+00 0.00E+00 0.000

Monday, March 07, 2011 Page 11 of 18
Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000291 0.0000000052 0.000000019 0.000

lb/mmBtuO2 4.02E-12 7.35E-13 2.63E-12 0.000

ng/dscm 4.30E-03 7.85E-04 2.81E-03 0.003

ng/dscm@7%O2 4.67E-03 8.52E-04 3.05E-03 0.003

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0 0.0000000043 0.0000000069 0.000

lb/mmBtuO2 0.00E+00 6.08E-13 9.54E-13 0.000

ng/dscm 0.00E+00 6.49E-04 1.02E-03 0.001

ng/dscm@7%O2 0.00E+00 7.05E-04 1.11E-03 0.001

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000972 0.0000000257 0.0000000348 0.000

lb/mmBtuO2 1.34E-11 3.63E-12 4.81E-12 0.000

ng/dscm 1.44E-02 3.88E-03 5.14E-03 0.008

ng/dscm@7%O2 1.56E-02 4.21E-03 5.58E-03 0.008

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.0000000516 0.0000000277 0.0000000554 0.000

lb/mmBtuO2 7.14E-12 3.92E-12 7.66E-12 0.000

ng/dscm 7.62E-03 4.18E-03 8.18E-03 0.007

ng/dscm@7%O2 8.27E-03 4.54E-03 8.88E-03 0.007

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.0000001963 0.0000000662 0.0000000989 0.000

lb/mmBtuO2 2.71E-11 9.36E-12 1.37E-11 0.000

ng/dscm 2.90E-02 9.99E-03 1.46E-02 0.018

ng/dscm@7%O2 3.15E-02 1.08E-02 1.59E-02 0.019

Compound: Total PCBs

Average

RunNumber 1 2 3

Mass_mg 0.0000008217 0.0000006432 0.0000005506 0.000

lb/mmBtuO2 1.14E-10 9.09E-11 7.61E-11 0.000

ng/dscm 1.21E-01 9.71E-02 8.13E-02 0.100

ng/dscm@7%O2 1.31E-01 1.05E-01 8.83E-02 0.108

Compound: Total TEQ

Average

RunNumber 1 2 3

Mass_mg 0 0 0.000

lb/mmBtuO2 0.00E+00 0.00E+00 0.000

Monday, March 07, 2011 Page 12 of 18
Process Run Data

ng/dscm #Num!

ng/dscm@7%O2 #Num!

Monday, March 07, 2011 Page 13 of 18
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Heat Input 0 Million Btus 0

2 Heat Input 0 Million Btus 0

3 Heat Input 0 Million Btus 0

1 Average Heat Input 0 MMBtu/hr 0

2 Average Heat Input 0 MMBtu/hr 0

3 Average Heat Input 0 MMBtu/hr 0

1 Steam Output 0 1000 lb steam/hr 0

2 Steam Output 0 1000 lb steam/hr 0

3 Steam Output 0 1000 lb steam/hr 0

1 Synfuel Firing Rate 0 0

2 Synfuel Firing Rate 0 0

3 Synfuel Firing Rate 0 0

1 Petroleum Coke Firing Rate 0 0

2 Petroleum Coke Firing Rate 0 0

3 Petroleum Coke Firing Rate 0 0

1 Coal Gas Firing Rate 0 0

2 Coal Gas Firing Rate 0 0

3 Coal Gas Firing Rate 0 0

1 Fuel Oil Firing Rate 0 0

2 Fuel Oil Firing Rate 0 0

3 Fuel Oil Firing Rate 0 0

1 Flue Gas Flow Rate 0 dscfm 0

1 Pressure Drop Across FGD (if applicable) 0 in H20 0

1 FGD Scrubber Liquor pH 0 pH 0

1 FGD Scrubber Liquor Flow Rate 0 gal/min 0

1 Sorbent Type and Sorbent Injection Rate (if 

applicable)

0 lb/hr 0

1 Flue Gas Oxygen Content 0 % 0

1 Flue Gas Carbon Dioxide Content 0 % 0

1 Flue Gas Moisture Content 0 % 0

1 Flue Gas Sampling Point Temperature 0 Deg F 0

1 Flue Gas Pressure 0 atm 0

1 Standard Pressure 0 atm 0

1 Standard Temperature 0 Deg F 0

Monday, March 07, 2011 Page 14 of 18
APCD Run Data

Process Lab Run Data

1 Unit Gross Electrical Output 0 MW 0

1 Unit Net Electric Generation 0 MWh 0

Run Name Value UOM Comments

Target

Value

1 List all emissions control devices in order of 

process flow. Choose from

0 0

1 drop down lists. If not on list add description and 

provide detailed

0 0

1 desription in section 5a. 0 0

Run Name Value UOM Comments

1 See 4b Comments. 0

Monday, March 07, 2011 Page 15 of 18
Sampling / Stack Data Results Detail

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 12/13/2010 12/14/2010 12/15/2010

Run Start Time 8:45:00 AM 9:45:00 AM 8:45:00 AM

Run Finish Time 5:15:00 PM 6:15:00 PM 5:15:00 PM

Net Traversing Points 11 11 11

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.192 0.192 0.192 0.192

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.985 0.985 0.985 0.985

Barometric Pressure, inches of Mercury 29.85 29.81 29.85 29.837

Average Orifice Meter Differential, inches H2O 0.83 0.80 0.83 0.820

Dry Gas Meter Volume Sampled, cubic feet 251.146 249.036 251.146 250.443

Average Dry Gas Meter Temperature, °F 85.83 92.48 85.83 88.047

Dry Gas Meter Volume Sampled, dscf 239.226 234.030 239.226 237.494

Total Moisture Liquid collected, g 593 548.9 593 578.300

Volume of Water Vapor, standard cubic feet 27.91 25.84 27.91 27.220

Moisture Content of Stack Gas, % 10.45 9.94 10.45 10.280

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8955 0.9006 0.8955 0.897

Carbon Dioxide, % 10.3 10.3 10.3 10.300

Oxygen, % 8.1 8.1 8.1 8.100

Carbon Monoxide & Nitrogen, % 81.6 81.6 81.6 81.600

Fuel Factor 1.24 1.24 1.24

Dry Molecular Weight, lb/lb-Mole 29.97 29.97 29.97 29.970

Wet Molecular weight, lb/lb-Mole 28.72 28.78 28.72 28.740

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.92 29.88 29.92 29.907

Average Stack Gas Temperature, °F 262.29 262.83 262.29 262.470

Average Velocity Head, inches of H2O 0.8603882654

83701

0.835502055

024941

0.860388265

483701

0.852

Average Stack Gas Velocity, feet/second 61.07 60.18 61.07 60.773

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 103.3 102.2 103.3 102.933

Percent Excess Air, % 60.3 60.3 60.3 60.300

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 16 of 18
Location Stack Exit - Method 29 

Average

Run Number 1 2 3

Test Date 12/16/2010 12/16/2010 2/17/2010

Run Start Time 8:20:00 AM 2:08:00 PM 8:45:00 AM

Run Finish Time 12:50:00 PM 6:38:00 PM 1:15:00 PM

Net Traversing Points 24 24 24

Net Run Time, minutes 240 240 240

Nozzle Diameter, inches 0.195 0.195 0.195 0.195

Pitot Tube Coefficient 0.84 0.84 0.84 0.840

Dry Gas Meter Calibration Factor 0.985 0.985 0.985 0.985

Barometric Pressure, inches of Mercury 30 30 30.1 30.033

Average Orifice Meter Differential, inches H2O 0.86 0.80 0.81 0.823

Dry Gas Meter Volume Sampled, cubic feet 126.933 121.949 124.638 124.507

Average Dry Gas Meter Temperature, °F 84.35 85.54 89.29 86.393

Dry Gas Meter Volume Sampled, dscf 121.854 116.797 118.955 119.202

Total Moisture Liquid collected, g 305 293.1 292.1 296.733

Volume of Water Vapor, standard cubic feet 14.36 13.80 13.75 13.970

Moisture Content of Stack Gas, % 10.54 10.57 10.36 10.490

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.8946 0.8943 0.8964 0.895

Carbon Dioxide, % 10.3 10.6 10.5 10.467

Oxygen, % 8.1 7.7 7.8 7.867

Carbon Monoxide & Nitrogen, % 81.6 81.7 81.7 81.667

Fuel Factor 1.24 1.25 1.25

Dry Molecular Weight, lb/lb-Mole 29.97 30.00 29.99 29.987

Wet Molecular weight, lb/lb-Mole 28.71 28.73 28.75 28.730

Flue Gas Static Pressure, inches of H2O 1 1 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 30.07 30.07 30.17 30.103

Average Stack Gas Temperature, °F 261.54 261.00 261.08 261.207

Average Velocity Head, inches of H2O 0.8444979145

86015

0.776975249

709904

0.792443828

307631

0.805

Average Stack Gas Velocity, feet/second 60.33 57.83 58.29 58.817

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm 0.0 0.0 0.0 0.000

Actual Wet Volumetric Flue Gas Flow Rate, acfm 0.0 0.0 0.0 0.000

Percent Isokinetic of Sampling Rate, % 102.8 102.7 103.2 102.900

Percent Excess Air, % 60.3 55.5 56.6 57.467

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Monday, March 07, 2011 Page 17 of 18
Location Stack Exit - OTM - 27/28

Average

Run Number 1 2 3

Test Date 12/15/2010 12/16/2010 12/16/2010

Run Start Time 12:00:00 AM

Run Finish Time 11:29:00 PM

Net Traversing Points 7 1 1

Net Run Time, minutes 120

Nozzle Diameter, inches 0.184 0.184

Pitot Tube Coefficient 0.84 0.840

Dry Gas Meter Calibration Factor 1.02 1.020

Barometric Pressure, inches of Mercury 29.8 29.800

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet 52.432 0.000 0.000 17.477

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g 132.8 0 0 44.267

Volume of Water Vapor, standard cubic feet 6.25 0.00 0.00 2.083

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, % 10.2 10.200

Oxygen, % 8.1 8.100

Carbon Monoxide & Nitrogen, % 81.7 81.700

Fuel Factor 1.25

Dry Molecular Weight, lb/lb-Mole 29.96

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O 1 1.000

Absolute Flue Gas Pressure, inches of Mercury 29.87

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O 0.8636087722

78662

0.864

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet 0.000 0.000 0.000 0.000

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, % 60.1

F-Factor, dscfm/MMBtu @ %O2 9190 0 0 3,063.333

Round Duct Diameter, inches 0 0 0

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 0 0 3,440.000

Fc 1420 0 0 473.333

Monday, March 07, 2011 Page 18 of 18