Quarterly Groundwater Monitoring 

Report-Outside (Non-Tunnel) Wells

RED HILL BULK FUEL STORAGE FACILITY, JOINT BASE PEARL 

HARBOR-HICKAM, O‘AHU, HAWAI‘I

Latitude: 21°22’15”N

Longitude: 157°53’33”W

DOH Facility ID No. 9-102271

DOH Release ID No. 99051, 010011, 020028

September 2012

Department of the Navy

Naval Facilities Engineering Command, Hawai‘i

400 Marshall Road

JBPHH HI 96860-3139

Environmental Technical Services

Contract Number N62742-08-D-1930, CTO HC21

Quarterly Groundwater Monitoring 

Report-Outside (Non-Tunnel) Wells

RED HILL BULK FUEL STORAGE FACILITY, JOINT BASE PEARL 

HARBOR-HICKAM, O‘AHU, HAWAI‘I

Latitude: 21°22’15”N

Longitude: 157°53’33”W

DOH Facility ID No. 9-102271

DOH Release ID No. 99051, 010011, 020028

September 2012

Prepared for:

Department of Navy

Naval Facilities Engineering Command, Hawai‘i

400 Marshall Road

JBPHH HI 96860-3139

Prepared by:

Environet, Inc.

1286 Queen Emma Street

Honolulu, HI 96813

Prepared under:

Environmental Technical Services

Contract Number N62742-08-D-1930, CTO HC21

Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Table of Contents

September 2012

i

Table of Contents

List of Acronyms........................................................................................................................... iii

Executive Summary ........................................................................................................................v

Section 1 Introduction ................................................................................................................ 1-1

1.1 Project Objective.............................................................................................................. 1-1

1.2 Background...................................................................................................................... 1-1

1.2.1 Site Description....................................................................................................... 1-2

1.2.2 Facility Information ................................................................................................ 1-2

1.2.3 UST Information..................................................................................................... 1-5

1.2.4 Regulatory Updates................................................................................................. 1-5

1.3 Previous Reports.............................................................................................................. 1-6

Section 2 Monitoring Activities .................................................................................................. 2-1

2.1 Groundwater Gauging...................................................................................................... 2-1

2.2 Groundwater Sampling .................................................................................................... 2-1

2.2.1 Monitoring Well Purging........................................................................................ 2-1

2.2.2 Groundwater Sample Collection............................................................................. 2-1

2.2.3 Sample Management and Shipment........................................................................ 2-2

2.3 Analytical Program .......................................................................................................... 2-2

2.4 Field Quality Control Samples......................................................................................... 2-2

2.5 Laboratory Quality Control Samples............................................................................... 2-2

2.6 Equipment Decontamination ........................................................................................... 2-3

2.7 Investigation-Derived Waste Management...................................................................... 2-3

Section 3 Groundwater Analytical Results ................................................................................ 3-1

3.1 Summary of Groundwater Analytical Results................................................................. 3-1

3.1.1 Data Quality Control Results.................................................................................. 3-1

3.2 Groundwater Contaminant Trend .................................................................................... 3-1

Section 4 Summary, Conclusions, and Recommendations....................................................... 4-1

4.1 Summary.......................................................................................................................... 4-1

4.2 Conclusions...................................................................................................................... 4-1

4.3 Recommendations............................................................................................................ 4-3

Section 5 References................................................................................................................... 5-1

Tables

Table 1-1: Outside Monitoring Well Information ...................................................................... 1-5

Table 3-1: Analytical Results for Quarterly Groundwater Monitoring-Outside (Non-Tunnel) 

Wells, July 2012 ........................................................................................................ 3-5

Table 3-2: Field QC Results-Outside Wells, July 2012.............................................................. 3-7

Table 3-3: Historical and Current Groundwater Sample Analytical Results, August 2009 

through July 2012...................................................................................................... 3-9
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Table of Contents

September 2012

ii

Figures

Figure 1-1: Groundwater Monitoring Well Location Map......................................................... 1-3

Appendices

Appendix A: DOH Correspondence 

Appendix B: Field Notebook 

Appendix C: Groundwater Sampling Logs

Appendix D: Laboratory Analytical Results, July 2012 (on CD-ROM)
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

List of Acronyms

September 2012

iii

List of Acronyms

μg/L micrograms per liter

% percent

amsl above mean sea level

bTOC below top of casing

COPC chemical of potential concern

CTO Contract Task Order

DL detection limit or method detection limit (MDL)

DLNR Department of Land and Natural Resources

DOH State of Hawai‘i Department of Health

DON Department of the Navy

DRO diesel range organics

dup duplicate

EAL Environmental Action Level

EPA U.S. Environmental Protection Agency

EPH extractable petroleum hydrocarbon

F-76 marine diesel fuel

FLC Fleet Logistics Center

GRO gasoline range organics

HAR Hawai‘i Administrative Rules

IDW investigation-derived waste

J Estimated result. Indicates that the compound was identified, but the 

concentration was above the DL and below the LOQ.

JBPHH Joint Base Pearl Harbor-Hickam

JP Jet Propellant

LOD limit of detection

LOQ limit of quantitation or reporting limit (RL)

MADEP Massachusetts Department of Environmental Protection

MS matrix spike

MSD matrix spike duplicate

NA not available

NAVFAC Naval Facilities Engineering Command

NAVSUP United States Naval Supply Systems Command

ND not detected

PAHs polycyclic aromatic hydrocarbons

pH hydrogen activity

PHWS Pearl Harbor Water System

PPE personal protective equipment

Q data qualifier

QC quality control

RHSF Red Hill Bulk Fuel Storage Facility

RPD relative percent difference

TEC The Environmental Company, Inc.

TPH total petroleum hydrocarbons

U Indicates the compound or analyte was analyzed for, but not detected. 

The result is reported as ND.

U.S. United States

USGS United States Geological Survey

UST underground storage tank

VOC volatile organic compound
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

List of Acronyms

September 2012

iv

This page is intentionally left blank.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Executive Summary

September 2012

v

Executive Summary

There are 18 active and two inactive, 12.5 million gallon capacity, field-constructed underground 

storage tanks (USTs) located at the Red Hill Bulk Fuel Storage Facility (RHSF). Previous 

environmental site investigations indicated a release had occurred and contaminated the 

groundwater underlying the RHSF.

The United States (U.S.) Navy implemented a groundwater monitoring program, which includes 

collecting quarterly groundwater samples from U.S. Navy Well 2254-01 (RHMW2254-01) and 

four groundwater monitoring wells (RHMW01, RHMW02, RHMW03, and RHMW05) installed 

in the RHSF lower access tunnel. The U.S. Navy Well 2254-01 is located approximately 3,000 

feet downgradient from the RHSF and provides approximately 24 percent (%) of the potable 

water to the Pearl Harbor Water System (PHWS). The groundwater samples are analyzed for 

petroleum constituents and compared against State of Hawai‘i Department of Health (DOH) 

Drinking Water Environmental Action Levels (EALs) (DOH, 2009).

In response to increasing concentrations of chemicals of potential concern (COPCs) in the 

groundwater monitoring wells within the facility (specifically RHMW02) during 2008, plans 

were made to conduct four quarterly monitoring events starting in August 2009 and ending in 

April 2010 at the following outside (non-tunnel) monitoring well locations:

RHMW04;

Oily Waste Disposal Facility Monitoring Well 01 (OWDFMW01); and

Hālawa Deep Well 2253-03 (HDMW2253-03).

The four consecutive quarterly monitoring events indicated that all COPC concentrations were 

below the EALs for samples collected at monitoring well RHMW04. In January 2010, 

concentrations of total petroleum hydrocarbons (TPH) diesel range organics (DRO) were above 

the EALs at OWDFMW01 and HDMW2253-03. As a result, quarterly monitoring was 

discontinued at RHMW04 and continued at the two remaining outside monitoring wells. This 

groundwater monitoring report presents the analytical results for samples collected on July 19, 

2012 at the two outside monitoring wells (OWDFMW01 and HDMW2253-03).

Laboratory analytical results indicate that all COPC concentrations during the July 2012 

monitoring event were below the DOH Drinking Water EALs. Benzene was detected at a 

concentration of 1.3 micrograms per liter (μg/L) in monitoring well OWDFMW01. Acetone and 

2-butanone were detected at estimated concentrations of 2.3 μg/L and 1.0 μg/L, respectively in 

monitoring well OWDFMW01. All other COPCs were not detected at or above the limits of 

detection (LODs) or the limits of quantitation (LOQs). LODs and LOQs were below the EALs 

for the majority of COPCs. In the case where an EAL for a specific COPC is less than the LOQ, 

it is generally acceptable to consider the LOQ in place of the EAL (DOH, 2009).

All COPC concentrations prior to the April 2012 monitoring event had been below EALs for at 

least the past six consecutive quarterly monitoring events dating back to October 2010. The 

April 2012 event showed TPH-DRO concentrations increase to levels above the DOH Drinking 
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Executive Summary

September 2012

vi

Water EAL in monitoring well OWDFMW01 and above the DOH Gross Contamination EAL in 

both monitoring wells. However, the elevated TPH-DRO concentrations were mainly due to 

non-diesel hydrocarbons detected by the analytical method. Massachusetts Department of 

Environmental Protection (MADEP) extractable petroleum hydrocarbon (EPH) analytical results 

in the October 2011 monitoring event indicated that the detected hydrocarbons were most likely 

from non-petroleum sources. The reported TPH-DRO concentrations are not considered 

TPH-DRO, but non-petroleum hydrocarbons. During the July 2012 monitoring event,

TPH-DRO concentrations in both wells decreased to non-detectable levels.

The groundwater monitoring program results indicate that concentrations of COPCs detected 

within the facility are not impacting the two outside monitoring wells. It is recommended that 

quarterly sampling remain the same and attention continue to be paid to COPC concentrations at 

both monitoring wells for signs of contaminant migration.

.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 1

Introduction

September 2012

1-1

Section 1 Introduction

This report presents the results of the July 2012 quarterly groundwater monitoring event at the 

two outside monitoring wells (OWDFMW01 and HDMW2253-03) at the RHSF, Joint Base 

Pearl Harbor-Hickam (JBPHH), O‘ahu, Hawai‘i (Figure 1-1). The groundwater monitoring was 

performed by Environet for the Department of the Navy (DON), Naval Facilities Engineering 

Command (NAVFAC) Hawai‘i under Environmental Technical Services, Contract Number 

N62742-08-D-1930, Contract Task Order (CTO) HC21.

This groundwater monitoring event is considered supplemental to the quarterly groundwater 

monitoring program conducted within the tunnels of the RHSF. This supplemental groundwater 

monitoring was conducted in response to increasing concentrations of COPCs in a groundwater 

monitoring well within the RHSF, specifically RHMW02, during the October 2008 groundwater 

monitoring event. The field activities performed for the July 2012 quarterly groundwater 

monitoring event were conducted in accordance with the procedures described in the Work Plan, 

Long-Term Monitoring, Red Hill Bulk Fuel Storage Facility, Pearl Harbor, O‘ahu, Hawai‘i 

(Environet, 2010).

1.1 Project Objective

The groundwater monitoring was performed to evaluate the presence of COPCs in groundwater 

surrounding the RHSF. The groundwater monitoring was conducted to ensure that the DON 

remains in compliance with DOH UST release response requirements as described in Hawai‘i 

Administrative Rules (HAR) 11-281 Subchapter 7, Release Response Action.

1.2 Background

The U.S. Navy implemented a groundwater monitoring program, which includes collecting 

quarterly groundwater samples from U.S. Navy Well 2254-01 (RHMW2254-01) and four 

groundwater monitoring wells (RHMW01, RHMW02, RHMW03, and RHMW05) installed in 

the RHSF lower access tunnel. The U.S. Navy Well 2254-01 is located approximately 3,000 feet 

downgradient from the RHSF and provides approximately 24% of the potable water to the 

PHWS. The groundwater samples are analyzed for petroleum constituents and compared against 

DOH Drinking Water EALs (DOH, 2009).

In response to increasing concentrations of COPCs in the groundwater monitoring wells within 

the facility (specifically RHMW02) during 2008, plans were made to conduct four quarterly 

monitoring events starting in August 2009 and ending in April 2010 at the following outside 

(non-tunnel) monitoring well locations:

RHMW04; 

Oily Waste Disposal Facility Monitoring Well 01 (OWDFMW01); and

Hālawa Deep Well 2253-03 (HDMW2253-03).
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 1

Introduction

September 2012

1-2

The four consecutive quarterly monitoring events indicated that all COPC concentrations were 

below the EALs for samples collected at monitoring well RHMW04. In January 2010,

concentrations of TPH-DRO were above the EALs at OWDFMW01 and HDMW2253-03. As a 

result, quarterly monitoring was discontinued at RHMW04 and continued at the two remaining 

outside monitoring wells. This groundwater monitoring report presents the analytical results for 

samples collected on July 19, 2012 at the two outside monitoring wells (OWDFMW01 and 

HDMW2253-03). The following sections provide a description of the site and information on 

the RHSF and USTs.

1.2.1 Site Description

The RHSF is located on the island of O‘ahu, Hawai‘i, approximately 2.5 miles northeast of Pearl 

Harbor in Hālawa Heights (Figure 1-1). Land adjacent to the north of the RHSF is occupied by 

the Hālawa Correctional Facility and private businesses. Land to the south and west of the 

facility includes the Coast Guard Reservation and other residential neighborhoods. Moanalua 

Valley is located east of the facility (Environet, 2010).

The Navy Public Works Department operates a potable water infiltration tunnel approximately 

1,550 feet hydraulically downgradient from the RHSF (Environet, 2010). The U.S. Navy Well 

2254-01 is located approximately 3,000 feet downgradient (west) of the RHSF and provides 

approximately 24% of the potable water to the PHWS, which serves approximately 52,200 

military consumers (The Environmental Company, Inc. (TEC), 2008).

1.2.2 Facility Information

The RHSF consists of 18 active and two inactive USTs operated by the United States Naval 

Supply Systems Command (NAVSUP) Fleet Logistics Center (FLC) Pearl Harbor. Each UST 

has a capacity of 12.5 million gallons. The RHSF is located approximately 100 feet above the 

basal aquifer (Dawson Group, Inc., 2006).

In 2002, the U.S. Navy installed a groundwater monitoring well (RHMW01) into the basal 

aquifer, directly downgradient from the RHSF, within the lower access tunnel. Groundwater 

samples from this well indicated that petroleum from the RHSF has migrated to the basal aquifer 

(AMEC Earth and Environmental, Inc., 2002). In 2005, the U.S. Navy began quarterly 

monitoring of the aquifer to protect their downgradient drinking water resource associated with 

the U.S. Navy Well 2254-01.

By September 2005, the U.S. Navy had installed two more groundwater monitoring wells 

(RHMW02 and RHMW03) within the RHSF UST system, a groundwater monitoring well 

(RHMW04) north of the RHSF (adjacent to the U.S. Navy Firing Range), and a groundwater 

monitoring well within the U.S. Navy Well 2254-01 infiltration gallery (RHMW2254-01). Since 

2005, RHMW01, RHMW02, RHMW03, and RHMW2254-01 have been sampled quarterly for 

TPH-DRO, TPH-gasoline range organics (GRO), volatile organic compounds (VOCs), 

polycyclic aromatic hydrocarbons (PAHs), and dissolved lead.

Due to increasing concentrations of COPCs at the groundwater monitoring wells within the 

RHSF (specifically RHMW02) during 2008, response measures were warranted. In April 2009, 

another groundwater monitoring well (RHMW05) was installed within the lower access tunnel 
A@ A@ A@

A@

A@

A@

A@

A@

?@ ?@

?@ ?@

?@ ?@

?@ ?@

?@ ?@

?@ ?@

?@ ?@

?@ ?@

?@ ?@

!(

OWDFMW01

RHMW2254-01

RHMW05

RHMW01

RHMW02

RHMW03

HDMW2253-03

SVMP02

SVMP03

SVMP04

SVMP06

SVMP08

SVMP10

SVMP12

SVMP14

SVMP16

SVMP18

SVMP20

SVMP05

SVMP07

SVMP09

SVMP11

SVMP13

SVMP15

SVMP17

Hālawa Industrial Park

Hālawa Correctional Facility

Hālawa Stream

RHMW04

U.S. Navy Well 2254-01

Hālawa Shaft Board of Water

Supply Pump Station (2354-01)

Coast Guard

Reservation

Moanalua

Village

Navy Firing

Range

?@ Soil Vapor Monitoring Points

A@ Groundwater Monitoring Wells

!( Board of Water Supply Pump Station

Hālawa Correctional Facility

Red Hill Naval Reservation

Hālawa Stream

1,000 500 0 1,000

Feet

Figure 1-1

Groundwater Monitoring Well

Location Map

LEGEND

 ̄

USGS, 2005

SOURCE

Pearl Harbor

Quarterly Groundwater Monitoring

Report-Outside (Non-Tunnel) Wells,

Red Hill Bulk Fuel Storage Facility,

JBPHH, O'ahu, Hawai'i

Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 1

Introduction

September 2012

1-5

between RHMW01 and RHMW2254-01. It was installed to identify the extent of contaminant 

migration in groundwater before it reaches the infiltration gallery at RHMW2254-01.

Additionally, plans were made to sample three monitoring wells surrounding and outside of 

RHSF: RHMW04, OWDFMW01, and HDMW2253-03 (Figure 1-1 and Table 1-1). RHMW04 

was installed to evaluate groundwater within the basal aquifer upgradient from RHSF. 

OWDFMW01 (originally known as MW08) was installed into the basal aquifer in 1998 for a 

Phase II Remedial Investigation/Feasibility Study for the Red Hill Oily Waste Disposal Facility 

(Earth Tech, Inc., 2000). It is located geographically downgradient of the USTs and U.S. Navy 

Well 2254-01. HDMW2253-03 is controlled by the State of Hawai‘i Commission on Water 

Resource Management. HDMW2253-03 is located between the RHSF and the municipal 

drinking water supply well, which is operated by the City and County of Honolulu Board of 

Water Supply (Hālawa Shaft Pumping Station 2354-01) (Figure 1-1).

Table 1-1: Outside Monitoring Well Information

Groundwater 

Monitoring Well

bTOC Elevation 

(feet amsl)

Depth to Water 

(feet bTOC)

Total Depth of Well 

(feet)

RHMW04 313.03 --- 320

OWDFMW01 138.94 120.15 142.8

HDMW2253-03 225 207. 87* 1,575

Notes:

*Depth to water provided by the Department of Land and Natural Resources on July 19, 2012.

--- Depth to water was not gauged at RHMW04 on July 19, 2012 because it is no longer a part of the sampling program.

amsl - above mean sea level

bTOC - below top of casing

1.2.3 UST Information

The USTs were constructed in the early 1940s. The tanks were constructed of steel and currently 

contain Jet Propellant (JP)-5 fuel, JP-8, and marine diesel fuel (F-76). Previously, several tanks 

stored Navy Special Fuel Oil, Navy Distillate, aviation gasoline, and motor gasoline. Each tank 

measures approximately 245 feet in height and 100 feet in diameter. The upper domes of the 

tanks lie at depths varying between approximately 100 feet and 200 feet below the existing 

ground surface (TEC, 2006).

1.2.4 Regulatory Updates

During the summer and fall of 2008, DOH updated their EALs, which resulted in significant 

changes to the action levels associated with methylnaphthalenes. The drinking water toxicity 

EAL for these compounds was 240 μg/L. This concentration presumed that methylnaphthalenes 

were non-carcinogenic. Evidence that they are human carcinogens has now been accepted by the 

U.S. Environmental Protection Agency (EPA). As a result, DOH adopted more rigorous EALs 

of 4.7 μg/L for 1-methylnaphthalene and 24 μg/L for 2-methylnaphthalene, corresponding to a 

residential tap water scenario, and a one in a million cancer risk (DOH, 2009). Also, the 

drinking water EAL for naphthalene was increased from 6.2 μg/L to 17 μg/L (DOH, 2009). 

Finally, the DOH Drinking Water EAL for TPH-DRO was increased from 100 μg/L to 210 μg/L, 

although the DOH Groundwater Gross Contamination EAL for TPH-DRO remains 100 μg/L.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 1

Introduction

September 2012

1-6

1.3 Previous Reports

The following groundwater monitoring reports were previously submitted to the DOH for the 

groundwater monitoring wells within the RHSF:

1. Groundwater Sampling Report, First Quarter 2005 (submitted April 2005);

2. Groundwater Sampling Report, Second Quarter 2005 (submitted August 2005);

3. Groundwater Sampling Report, Third Quarter 2005 (submitted November 2005);

4. Groundwater Sampling Report, Fourth Quarter 2005 (submitted February 2006);

5. Groundwater Monitoring Results, July 2006 (submitted September 2006);

6. Groundwater Monitoring Results, December 2006 (submitted January 2007);

7. Groundwater Monitoring Results, March 2007 (submitted May 2007);

8. Groundwater Monitoring Results, June 2007 (submitted August 2007);

9. Groundwater Monitoring Results, September 2007 (submitted October 2007);

10. Groundwater Monitoring Results, January 2008 (submitted March 2008);

11. Groundwater Monitoring Results, April 2008 (submitted May 2008);

12. Groundwater Monitoring Results, July 2008 (submitted October 2008);

13. Groundwater Monitoring Results, October and December 2008 (submitted 

February 2009);

14. Groundwater Monitoring Results, February 2009 (submitted May 2009);

15. Groundwater Monitoring Results, May 2009 (submitted July 2009);

16. Groundwater Monitoring Results, July 2009 (submitted September 2009);

17. Groundwater Monitoring Results, October 2009 (submitted December 2009);

18. Groundwater Monitoring Results, January, February, and March 2010 (submitted 

April 2010);

19. Groundwater Monitoring Results, April 2010 (submitted May 2010); 

20. Groundwater Monitoring Results, July 2010 (submitted August 2010);

21. Groundwater Monitoring Results, October 2010 (submitted December 2010);

22. Groundwater Monitoring Results, January 2011 (submitted March 2011);

23. Groundwater Monitoring Results, April 2011 (submitted June 2011); 

24. Groundwater Monitoring Results, July 2011 (submitted September 2011);

25. Groundwater Monitoring Results, October 2011 (submitted December 2011);

26. Groundwater Monitoring Results, January-February 2012 (submitted March 

2012); and

27. Groundwater Monitoring Results, April 2012 (submitted July 2012).
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 1

Introduction

September 2012

1-7

The following groundwater monitoring reports were previously submitted to the DOH for the 

groundwater monitoring wells outside the RHSF:

1. Groundwater Monitoring Results, August 2009 (submitted September 2009);

2. Groundwater Monitoring Results, October 2009 (submitted December 2009);

3. Groundwater Monitoring Results, January 2010 (submitted April 2010);

4. Groundwater Monitoring Results, April 2010 (submitted May 2010); 

5. Groundwater Monitoring Results, July 2010 (submitted August 2010); 

6. Groundwater Monitoring Results, October 2010 (submitted December 2010);

7. Groundwater Monitoring Results, January 2011 (submitted March 2011);

8. Groundwater Monitoring Results, April 2011 (submitted June 2011); 

9. Groundwater Monitoring Results, July 2011 (submitted September 2011);

10. Groundwater Monitoring Results, October 2011 (submitted December 2011);

11. Groundwater Monitoring Results, January 2012 (submitted March 2012); and

12. Groundwater Monitoring Results, April 2012 (submitted July 2012).
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 1

Introduction

September 2012

1-8

This page is intentionally left blank.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 2

Monitoring Activities

September 2012

2-1

Section 2 Monitoring Activities

Groundwater monitoring was conducted on July 19, 2012 in accordance with the site specific 

Work Plan (Environet, 2010). Field activities were documented in the field notebook (Appendix 

B).

2.1 Groundwater Gauging

Groundwater gauging measurements were taken at the two monitoring wells (OWDFMW01 and 

HDMW2253-03) prior to purging and sample collection. A Solinst® water level meter was used 

to measure the depth to groundwater (to the nearest 0.01 foot) within monitoring well 

OWDFMW01, according to the procedures described in Procedure I-C-3, Monitoring Well 

Sampling (DON, 2007). The depth to groundwater for monitoring well HDMW2253-03 was 

measured by a Department of Land and Natural Resources (DLNR) employee prior to well 

purging (Table 1-1).

2.2 Groundwater Sampling

Groundwater samples were collected from the two monitoring wells according to the procedures 

described in Procedure I-C-3, Monitoring Well Sampling (DON, 2007).

2.2.1 Monitoring Well Purging

Due to the well construction characteristics of OWDFMW01 (total depth of 142.8 feet below top 

of casing (bTOC)) and HDMW2253-03 (large casing diameter of approximately 12 inches from 

the top of casing to approximately 50 feet below the groundwater surface, and the well is open 

[not cased] from approximately 50 feet bTOC to 1,575 feet bTOC), three well casing volumes 

were not purged prior to sampling. Instead, water was purged using disposable bailers until three 

or more successive water quality parameter measurements had stabilized within 10%. A Horiba® 

U-22 multi-parameter water quality meter was used to measure hydrogen activity (pH), 

temperature, specific conductivity, dissolved oxygen, turbidity, and oxidation reduction 

potential. Readings were recorded on Groundwater Sampling Log data sheets (Appendix C).

2.2.2 Groundwater Sample Collection

Groundwater samples were collected from OWDFMW01 using four-inch and two-inch 

disposable bailers directly into laboratory provided, specially cleaned sample containers. The 

dissolved lead sample was filtered in the field at OWDFMW01 and placed in a polyethylene 

bottle containing the appropriate preservative.

Groundwater samples were collected from HDMW2253-03 using four-inch and two-inch 

disposable bailers directly into laboratory provided, specially cleaned sample containers. Due to 

the well construction characteristics of HDMW2253-03, a grab sample was collected at a depth 

below the solid casing (which extends about 50 feet below the water table) and within the 

open-holed portion of the well. The dissolved lead sample was filtered in the field at 

HDMW2253-03 and placed in a polyethylene bottle containing the appropriate preservative.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 2

Monitoring Activities

September 2012

2-2

2.2.3 Sample Management and Shipment

Each sample container sent to the laboratory was assigned a project-specific chain-of-custody 

identification number and a descriptive identification number. The sample identifiers provided 

specific data unique to each sample and were entered into the field notebook. The samples were 

labeled according to the procedures described in Procedure III-E, Record Keeping, Sample 

Labeling, and Chain-of-Custody (DON, 2007).

Following sample collection and labeling, the sample containers were packaged with bubble 

wrap and placed into individual Ziploc bags, then immediately into insulated coolers with ice 

for preservation. The samples were shipped via FedEx to the laboratory on the same day of 

collection. The samples were managed under standard chain-of-custody protocol and 

documentation from collection to delivery to the laboratory. Sample handling, storage, and 

transport were performed according to the requirements described in Procedure III-F, Sample 

Handling, Storage, and Shipping (DON, 2007).

2.3 Analytical Program

During the July 2012 groundwater monitoring event, two sets of primary groundwater samples, 

one set of duplicate groundwater samples and one set of quality control (QC) groundwater 

samples were submitted to APPL, Inc. located in Clovis, California. Groundwater samples were 

analyzed for VOCs and TPH-GRO by EPA Method 8260B, TPH-DRO by EPA Method 8015B, 

PAHs by EPA Method 8270D SIM, and dissolved lead by EPA Method 6020. The results of the 

laboratory analyses are presented and discussed in Section 3.

2.4 Field Quality Control Samples 

Field QC procedures were followed to ensure viability and integrity of sample analytical data. 

Field duplicates were collected according to the procedures described in Procedure III-B, Field 

QC Samples (Water, Soil) (DON, 2007) and the Work Plan (Environet, 2010). Field duplicate 

samples were collected at a minimum of 10% of primary samples and analyzed for the same 

COPCs. Field rinsate samples were not required since disposable bailers were used.

2.5 Laboratory Quality Control Samples 

Laboratory QC samples were analyzed as part of the standard laboratory QC protocols as 

presented in the Work Plan (Environet, 2010). Laboratory QC for the groundwater monitoring 

event consisted of matrix spike (MS)/matrix spike duplicate (MSD) samples for organic analysis. 

Laboratory QC samples were collected and analyzed according to the procedures described in 

Procedure III-A Laboratory QC Samples (Water, Soil) (DON, 2007). Laboratory QC MS/MSD 

samples are an aliquot (i.e., a subset) of the field sample; they are not separate samples, but a 

special designation of an existing sample. Laboratory QC MS/MSD samples were analyzed for 

the same constituents as the standard samples. At a minimum, one MS/MSD sample pair was 

required per 20 samples, including duplicates.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 2

Monitoring Activities

September 2012

2-3

2.6 Equipment Decontamination 

Decontamination of monitoring equipment was performed to ensure data quality, to prevent 

cross contamination, and to prevent the potential introduction of contaminants into previously 

un-impacted areas. Decontamination of monitoring equipment (i.e., Solinst® water level meter 

and Horiba® U-22 water quality meter) was conducted between monitoring locations according 

to the procedures described in Procedure I-F, Equipment Decontamination (DON, 2007). 

Decontamination water generated at monitoring well OWDFMW01 was disposed of in the 

RHSF’s lower tunnel oil/water separator sump.

2.7 Investigation-Derived Waste Management 

Investigation-derived waste (IDW) was managed in accordance with the procedures described in 

Procedure I-A-6, IDW Management (DON, 2007). The various potential waste streams included 

the following: 

 personal protective equipment (PPE), including: nitrile gloves, etc.; 

 liquids, including: equipment rinse water and purged groundwater; and

 disposable sampling equipment and supplies, including: bailers, poly sheeting, etc.

Equipment rinse water and purge water from OWDFMW01 was disposed of in the RHSF’s 

lower tunnel oil/water separator sump. Purge water from monitoring well HDMW2253-03 was 

disposed of in the surrounding grass (as directed by DLNR) since it was of drinking water 

quality. Spent PPE and non-contaminated sample jars and bottles (acid-free) were disposed of 

on a daily basis as solid waste.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 2

Monitoring Activities

September 2012

2-4

This page is intentionally left blank.

 
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 3

Groundwater Analytical Results

September 2012

3-1

Section 3 Groundwater Analytical Results

This section provides a summary of analytical results for groundwater samples collected from 

the two outside monitoring wells on July 19, 2012. Complete analytical laboratory reports are 

provided in Appendix D. 

3.1 Summary of Groundwater Analytical Results

OWDFMW01

Benzene was detected in monitoring well OWDFMW01 at a concentration of 1.3 μg/L, which is 

below the DOH Drinking Water EAL (5 μg/L) and Groundwater Gross Contamination EAL (170 

μg/L). Acetone was detected in monitoring well OWDFMW01 at an estimated concentration of 

2.3 μg/L, which is below the DOH Drinking Water EAL (22,000 μg/L) and Groundwater Gross 

Contamination EAL (20,000 μg/L). 2-Butanone was detected in monitoring well OWDFMW01 

at an estimated concentration of 1.0 μg/L, which is below the DOH Drinking Water EAL (7,100 

μg/L) and Groundwater Gross Contamination EAL (8,400 μg/L) (Table 3-1).

No other COPCs were detected at or above the LODs and LOQs in monitoring well 

OWDFMW01. All LODs and LOQs were generally below the EALs. In the case where an EAL 

for a specific COPC is less than the LOQ, it is generally acceptable to consider the LOQ in place 

of the EAL (DOH, 2009).

HDMW2253-03

No COPCs were detected at or above the LODs and LOQs in HDMW2253-03. All LODs and 

LOQs were generally below the EALs (Table 3-1). In the case where an EAL for a specific 

COPC is less than the LOQ, it is generally acceptable to consider the LOQ in place of the EAL 

(DOH, 2009).

3.1.1 Data Quality Control Results

The laboratory QC results were all within the control limits. The relative percent difference 

(RPD) of field duplicates for all analytes were within the 50% criteria. The trip blank that 

accompanied the outside well samples did not contain detectable levels of any COPCs. 

Therefore, the data QC results indicate that the data obtained for this monitoring event are 

suitable for their intended use (Table 3-2).

3.2 Groundwater Contaminant Trend

Concentrations of PAHs and VOCs were previously not detected above the EALs in the August 

2009, October 2009, January 2010, April 2010, July 2010, October 2010, January 2011, April 

2011, July 2011, October 2011, January 2012, and April 2012 groundwater monitoring events. 

These constituents were also not detected above the EALs during this current groundwater 

monitoring event (July 2012).
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 3

Groundwater Analytical Results

September 2012

3-2

TPH-DRO concentrations in OWDFMW01 significantly decreased from January 2010 (1,490 

μg/L) to April 2010 (288 μg/L). The concentrations of TPH-DRO at this monitoring well have 

decreased to non-detect in the previous six (October 2010, January 2011, April 2011, July 2011, 

October 2011, and January 2012) consecutive monitoring events (Table 3-3). In the April 2012 

monitoring event, the TPH-DRO concentration increased to a level above the EAL. However, 

the elevated concentration was mainly due to non-diesel hydrocarbons detected by the analytical 

method. The concentration of TPH-DRO in OWDFMW01 decreased to non-detect during the 

July 2012 monitoring event.

The concentrations of TPH-DRO at HDMW2253-03 decreased to non-detect for eight 

consecutive groundwater monitoring events from April 2010 to January 2012 (Table 3-3). In the 

April 2012 monitoring event, the TPH-DRO concentration increased slightly to a level below the 

EAL. However, the elevated concentration was mainly due to non-diesel hydrocarbons detected 

by the analytical method. The concentration of TPH-DRO in HDMW2253-03 decreased to 

non-detect during the July 2012 monitoring event.

The October 2010 detection of acetone at an estimated concentration below the DOH Drinking 

Water EAL was the first at monitoring well OWDFMW01. Acetone was also detected at an 

estimated concentration in the trip blank sample in that same event. This suggested that acetone 

was introduced to the samples during transport to and from the laboratory and was not 

representative of groundwater at OWDFMW01. The concentration of acetone decreased to 

non-detect for five consecutive monitoring events from January 2011 to January 2012. Acetone 

was again detected at estimated concentrations at monitoring well OWDFMW01 in the April 

2012 and July 2012 monitoring events. The April 2012 and July 2012 detections marked the 

second and third events, respectively, in which acetone was detected at estimated concentrations

at the monitoring well. However, none of the trip blanks for April 2012 and July 2012

monitoring events contained traces of the analyte, indicating that acetone was present at very low 

levels in the groundwater.

The October 2010 detections of lead at concentrations below the DOH Drinking Water EAL 

were the first at these two monitoring wells (OWDFMW01 and HDMW2253-03). Lead was not 

detected in any of the samples in the January 2011 monitoring event or in April 2011. Estimated 

concentrations of lead below the DOH Drinking Water EAL were detected at both wells in the 

July 2011 monitoring event. Lead was detected in monitoring well HDMW2253-03 at a 

concentration below the DOH Drinking Water EAL and in monitoring well OWDFMW01 at an 

estimated concentration below the DOH Drinking Water EAL in the October 2011 monitoring 

event. Lead was detected at estimated concentrations below the DOH Drinking Water EAL in 

both monitoring wells in the January 2012 monitoring event. In the April 2012 monitoring 

event, lead was detected at a concentration below the DOH Drinking Water EAL at 

HDMW2253-03 and was not detected at OWDFMW01. Lead was not detected in either 

monitoring well during the July 2012 monitoring event. Lead concentrations in both monitoring 

wells have fluctuated below the DOH Drinking Water EAL. The concentrations at which lead 

has been detected were very low to be of concern relative to the DOH Drinking Water EAL.

The January 2011 detection of benzene at an estimated concentration below the DOH Drinking 

Water EAL in OWDFMW01 was the first at this monitoring well. Benzene was detected at an 

estimated concentration in the duplicate sample collected from OWDFMW01 in April 2011; 
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 3

Groundwater Analytical Results

September 2012

3-3

however, it was not detected in the July 2011 monitoring event. It was detected at an estimated 

concentration below the DOH Drinking Water EAL in HDMW2253-03 in the October 2011 

monitoring event. In the January 2012 monitoring event, benzene was detected at an estimated 

concentration below the Drinking Water EAL in monitoring well OWDFMW01. In the April 

2012 monitoring event, benzene was detected at estimated concentrations below the Drinking 

Water EAL at both OWDFMW01 and HDMW2253-03. Benzene was not detected in 

monitoring well HDMW2253-03 in the July 2012 monitoring event (Table 3-1). Concentrations 

of benzene increased at monitoring well OWDFMW01 in the July 2012 monitoring event, but to 

levels below the DOH Drinking Water EAL (Table 3-1). Benzene concentrations have 

fluctuated below the DOH Drinking Water EAL in monitoring wells HDMW2253-03 and 

OWDFMW01. The estimated concentrations at which benzene have been detected were very 

low to be of concern relative to the DOH Drinking Water EAL.

The April 2011 detections of xylenes and toluene below the DOH Drinking Water EALs in 

OWDFMW01 were the first at these monitoring wells. Xylenes and toluene were not detected in 

the July 2011, October 2011, January 2012, April 2012, and July 2012 monitoring events (Table 

3-1). Xylene and toluene concentrations have exhibited no trends in both monitoring wells. The 

April 2011 xylene and toluene detections were estimated concentrations and were very low to be 

of concern relative to the DOH Drinking Water EALs.

The July 2012 detection of 2-butanone below the DOH Drinking Water EAL in OWDFMW01 

was the first at the monitoring well. The detection was an estimated concentration and was very 

low to be of concern relative to the DOH Drinking Water EAL (Table 3-1).
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 3

Groundwater Analytical Results

September 2012

3-4

This page is intentionally left blank.
Table 3-1: Analytical Results for Quarterly Groundwater Monitoring-Outside (Non-Tunnel) Wells, July 2012

Result Q LOQ LOD DL Result Q LOQ LOD DL

EPA 8015B (Petroleum) TPH-DRO 210 100 ND U 150b 80.8 40.4 ND U 150 80.8 40.4

EPA 8260B (Petroleum) TPH-GRO 100 100 ND U 20.0 12.12 6.06 ND U 20.0 12.12 6.06

Acenaphthene 370 20 ND U 0.2 0.12 0.06 ND U 0.2 0.12 0.06

Acenaphthylene 240 2000 ND U 0.2 0.12 0.06 ND U 0.2 0.12 0.06

Anthracene 1800 22 ND U 0.2 0.10 0.05 ND U 0.2 0.10 0.05

Benzo(a)anthracene 0.092 4.7 ND U 0.2b 0.14 0.07 ND U 0.2b 0.14 0.07

Benzo(g,h,i)perylene 1500 0.13 ND U 0.2b 0.16 0.08 ND U 0.2b 0.16 0.08

Benzo(a)pyrene 0.2 0.81 ND U 0.2 0.12 0.06 ND U 0.2 0.12 0.06

Benzo(b)fluoranthene 0.092 0.75 ND U 0.2b 0.12 0.06 ND U 0.2b 0.12 0.06

Benzo(k)fluoranthene 0.92 0.4 ND U 0.2 0.14 0.07 ND U 0.2 0.14 0.07

Chrysene 9.2 1 ND U 0.2 0.10 0.05 ND U 0.2 0.10 0.05

Dibenzo(a,h)anthracene 0.0092 0.52 ND U 0.2b 0.10 0.05 ND U 0.2b 0.10 0.05

Fluoranthene 1500 130 ND U 0.2 0.16 0.08 ND U 0.2 0.16 0.08

Fluorene 240 950 ND U 0.2 0.12 0.06 ND U 0.2 0.12 0.06

Indeno(1,2,3-cd)pyrene 0.092 0.095 ND U 0.2b 0.14 0.07 ND U 0.2b 0.14 0.07

1,-Methylnaphthalene 4.7 10 ND U 0.2 0.12 0.06 ND U 0.2 0.12 0.06

2,-Methylnaphthalene 24 10 ND U 0.2 0.12 0.06 ND U 0.2 0.12 0.06

Naphthalene 17 21 ND U 0.2 0.10 0.05 ND U 0.2 0.10 0.05

Phenanthrene 240 410 ND U 0.2 0.14 0.07 ND U 0.2 0.14 0.07

Pyrene 180 68 ND U 0.2 0.16 0.08 ND U 0.2 0.16 0.08

1,1,1-Trichloroethane 200 970 ND U 1.0 0.28 0.14 ND U 1.0 0.28 0.14

1,1,2-Trichloroethane 5 50,000 ND U 1.0 0.40 0.20 ND U 1.0 0.40 0.20

1,1-Dichloroethane 2.4 50,000 ND U 1.0 0.38 0.19 ND U 1.0 0.38 0.19

1,1-Dichloroethylene 

(1,1-Dichloroethene) 7 1,500 ND U 1.0 0.60 0.30 ND U 1.0 0.60 0.30

1,2,3-Trichloropropane 0.6 50,000 ND U 2.0b 0.78 0.39 ND U 2.0b 0.78 0.39

1,2,4-Trichlorobenzene 70 3,000 ND U 1.0 0.42 0.21 ND U 1.0 0.42 0.21

1,2-Dibromo-3-chloropropane 0.04 10 ND U 2.0b 1.52 0.76 ND U 2.0b 1.52 0.76

1,2-Dibromoethane 0.04 50,000 ND U 1.0b 0.40 0.20 ND U 1.0b 0.40 0.20

1,2-Dichlorobenzene 600 10 ND U 1.0 0.34 0.17 ND U 1.0 0.34 0.17

1,2-Dichloroethane 0.15 7,000 ND U 1.0b 0.28 0.14 ND U 1.0b 0.28 0.14

1,2-Dichloropropane 5 10 ND U 1.0 0.34 0.17 ND U 1.0 0.34 0.17

1,3-Dichlorobenzene 180 5 ND U 1.0 0.22 0.11 ND U 1.0 0.22 0.11

1,3-Dichloropropene (total of 

cis/trans) 0.43 50,000 ND U 1.0b 0.36 0.18 ND U 1.0 0.36 0.18

1,4-Dichlorobenzene 75 5 ND U 1.0 0.38 0.19 ND U 1.0 0.38 0.19

Acetone 22,000 20,000 2.3 J 10.0 1.90 0.95 ND U 10.0 1.90 0.95

Benzene 5 170 1.3 1.0 0.32 0.16 ND U 1.0 0.32 0.16

Bromodichloromethane 0.12 50,000 ND U 1.0b 0.28 0.14 ND U 1.0b 0.28 0.14

Bromoform 80 510 ND U 1.0 0.28 0.14 ND U 1.0 0.28 0.14

Bromomethane 8.7 50,000 ND U 2.0 0.48 0.24 ND U 2.0 0.48 0.24

Carbon Tetrachloride 5 520 ND U 1.0 0.20 0.10 ND U 1.0 0.20 0.10

Chlorobenzene 100 50 ND U 1.0 0.42 0.21 ND U 1.0 0.42 0.21

Chloroethane 21,000 16 ND U 1.0 0.42 0.21 ND U 1.0 0.42 0.21

Chloroform 70 2,400 ND U 1.0 0.14 0.07 ND U 1.0 0.14 0.07

Chloromethane 1.8 50,000 ND U 1.0 0.84 0.42 ND U 1.0 0.84 0.42

cis-1,2-Dichloroethylene (cis1,2-Dichloroethene) 70 50,000 ND U 1.0 0.32 0.16 ND U 1.0 0.32 0.16

Dibromochloromethane 

(Chlorodibromomethane) 0.16 50,000 ND U 1.0b 0.38 0.19 ND U 1.0b 0.38 0.19

Ethylbenzene 700 30 ND U 1.0 0.46 0.23 ND U 1.0 0.46 0.23

Hexachlorobutadiene 0.86 6 ND U 1.0b 0.38 0.19 ND U 1.0 0.38 0.19

Methyl ethyl ketone 

(2-Butanone) 7,100 8,400 1.0 J 10.0 1.20 0.60 ND U 10.0 1.20 0.60

Methyl isobutyl ketone 

(4-Methyl-2-pentanone) 2,000 1,300 ND U 10.0 3.80 1.90 ND U 10.0 3.80 1.90

Methyl tert-butyl Ether 12 5 ND U 1.0 0.52 0.26 ND U 1.0 0.52 0.26

Methylene chloride 4.8 9,100 ND U 5.0b 0.70 0.35 ND U 5.0 0.70 0.35

Styrene 100 10 ND U 1.0 0.50 0.25 ND U 1.0 0.50 0.25

Tetrachloroethane, 1,1,1,2- 0.52 50,000 ND U 1.0b 0.26 0.13 ND U 1.0 0.26 0.13

Tetrachloroethane, 1,1,2,2- 0.067 500 ND U 1.0b 0.20 0.10 ND U 1.0b 0.20 0.10

Tetrachloroethylene 

(Tetrachloroethene) 5 170 ND U 1.0 0.48 0.24 ND U 1.0 0.48 0.24

Toluene 1,000 40 ND U 1.0 0.34 0.17 ND U 1.0 0.34 0.17

trans-1,2-Dichloroethylene 

(trans-1,2-Dichloroethene) 100 260 ND U 1.0 0.38 0.19 ND U 1.0 0.38 0.19

Trichloroethylene 

(Trichloroethene) 5 310 ND U 1.0 0.32 0.16 ND U 1.0 0.32 0.16

Vinyl chloride 2 3,400 ND U 1.0 0.46 0.23 ND U 1.0 0.46 0.23

Xylenes 10,000 20 ND U 1.0 0.38 0.19 ND U 1.0 0.38 0.19

EPA 6020 Lead 15 5,000 ND U 0.5 0.22 0.11 ND U 0.5 0.22 0.11

Notes:

DRO - diesel range organics

GRO - gasoline range organics

LOD - limit of detection

LOQ - limit of quantitation or reporting limit (RL)

ND - not detected

PAHs - polycyclic aromatic hydrocarbons

Q - data qualifier

TPH - total petroleum hydrocarbons

VOC - volatile organic compound

Bold - Result exceeds one or both DOH EALs

J - Estimated result. Indicates that the compound was identified, but the concentration was above the DL and below the LOQ.

U - Indicates the compound or analyte was analyzed for, but not detected. The result is reported as ND.

(ES083)

EPA 8260B (VOCs)

a DOH EALs (DOH, 2009): Table D-1b. Groundwater Action Levels (Groundwater is a current or potential drinking water resource; surface water body is not located within 150 meters of release site).

b In the case where an EAL for a specific chemical is less than the LOQ for a commercial laboratory, it is generally acceptable to consider the LOQ in place of the action level (DOH, Evaluation of 

Environmental Hazards at Sites with Contaminated Soil and Groundwater 2008, updated March 2009). 

All units are in micrograms per liter (μg/L).

DL - detection limit or method detection limit (MDL)

HDMW2253-03 

(ES084)

OWDFMW01 

EPA 8270D SIM (PAHs)

Method Chemical

DOH Drinking Water 

EALs for Human 

Toxicitya 

DOH Groundwater 

Gross Contamination 

EALsa 

Table 3-2: Field QC Results-Outside Wells, July 2012

Q LOQ LOD DL Q LOQ LOD DL Result Q LOQ LOD DL

EPA 8015B (Petroleum) TPH-DRO 210 100 U 150b 80.8 40.4 U 150b 80.8 40.4 0 -- -- -- -- --

EPA 8260B (Petroleum) TPH-GRO 100 100 U 20.0 12.12 6.06 ND U 20.0 12.12 6.06 0 ND U 20.0 12.12 6.06

Acenaphthene 370 20 U 0.2 0.12 0.06 ND U 0.2 0.12 0.06 0 -- -- -- -- --

Acenaphthylene 240 2000 U 0.2 0.12 0.06 ND U 0.2 0.12 0.06 0 -- -- -- -- --

Anthracene 1800 22 U 0.2 0.10 0.05 ND U 0.2 0.10 0.05 0 -- -- -- -- --

Benzo(a)anthracene 0.092 4.7 U 0.2b 0.14 0.07 ND U 0.2b 0.14 0.07 0 -- -- -- -- --

Benzo(g,h,i)perylene 1500 0.13 U 0.2b 0.16 0.08 ND U 0.2b 0.16 0.08 0 -- -- -- -- --

Benzo(a)pyrene 0.2 0.81 U 0.2 0.12 0.06 ND U 0.2 0.12 0.06 0 -- -- -- -- --

Benzo(b)fluoranthene 0.092 0.75 U 0.2b 0.12 0.06 ND U 0.2b 0.12 0.06 0 -- -- -- -- --

Benzo(k)fluoranthene 0.92 0.4 U 0.2 0.14 0.07 ND U 0.2 0.14 0.07 0 -- -- -- -- --

Chrysene 9.2 1 U 0.2 0.10 0.05 ND U 0.2 0.10 0.05 0 -- -- -- -- --

Dibenzo(a,h)anthracene 0.0092 0.52 U 0.2b 0.10 0.05 ND U 0.2b 0.10 0.05 0 -- -- -- -- --

Fluoranthene 1500 130 U 0.2 0.16 0.08 ND U 0.2 0.16 0.08 0 -- -- -- -- --

Fluorene 240 950 U 0.2 0.12 0.06 ND U 0.2 0.12 0.06 0 -- -- -- -- --

Indeno(1,2,3-cd)pyrene 0.092 0.095 U 0.2b 0.14 0.07 ND U 0.2b 0.14 0.07 0 -- -- -- -- --

1,-Methylnaphthalene 4.7 10 U 0.2 0.12 0.06 ND U 0.2 0.12 0.06 0 -- -- -- -- --

2,-Methylnaphthalene 24 10 U 0.2 0.12 0.06 ND U 0.2 0.12 0.06 0 -- -- -- -- --

Naphthalene 17 21 U 0.2 0.10 0.05 ND U 0.2 0.10 0.05 0 -- -- -- -- --

Phenanthrene 240 410 U 0.2 0.14 0.07 ND U 0.2 0.14 0.07 0 -- -- -- -- --

Pyrene 180 68 U 0.2 0.16 0.08 ND U 0.2 0.16 0.08 0 -- -- -- -- --

1,1,1-Trichloroethane 200 970 U 1.0 0.28 0.14 ND U 1.0 0.28 0.14 0 ND U 1.0 0.28 0.14

1,1,2-Trichloroethane 5 50,000 U 1.0 0.40 0.20 ND U 1.0 0.40 0.20 0 ND U 1.0 0.40 0.20

1,1-Dichloroethane 2.4 50,000 U 1.0 0.38 0.19 ND U 1.0 0.38 0.19 0 ND U 1.0 0.38 0.19

1,1-Dichloroethylene 

(1,1-Dichloroethene) 7 1,500 U 1.0 0.60 0.30 ND U 1.0 0.60 0.30 0 ND U 1.0 0.60 0.30

1,2,3-Trichloropropane 0.6 50,000 U 2.0b 0.78 0.39 ND U 2.0b 0.78 0.39 0 ND U 2.0b 0.78 0.39

1,2,4-Trichlorobenzene 70 3,000 U 1.0 0.42 0.21 ND U 1.0 0.42 0.21 0 ND U 1.0 0.42 0.21

1,2-Dibromo-3-

chloropropane 0.04 10 U 2.0b 1.52 0.76 ND U 2.0b 1.52 0.76 0 ND U 2.0b 1.52 0.76

1,2-Dibromoethane 0.04 50,000 U 1.0b 0.40 0.20 ND U 1.0b 0.40 0.20 0 ND U 1.0b 0.40 0.20

1,2-Dichlorobenzene 600 10 U 1.0 0.34 0.17 ND U 1.0 0.34 0.17 0 ND U 1.0 0.34 0.17

1,2-Dichloroethane 0.15 7,000 U 1.0b 0.28 0.14 ND U 1.0b 0.28 0.14 0 ND U 1.0b 0.28 0.14

1,2-Dichloropropane 5 10 U 1.0 0.34 0.17 ND U 1.0 0.34 0.17 0 ND U 1.0 0.34 0.17

1,3-Dichlorobenzene 180 5 U 1.0 0.22 0.11 ND U 1.0 0.22 0.11 0 ND U 1.0 0.22 0.11

1,3-Dichloropropene (total of 

cis/trans) 0.43 50,000 U 1.0b 0.36 0.18 ND U 1.0b 0.36 0.18 0 ND U 1.0 0.36 0.18

1,4-Dichlorobenzene 75 5 U 1.0 0.38 0.19 ND U 1.0 0.38 0.19 0 ND U 1.0 0.38 0.19

Acetone 22,000 20,000 U 10.0 1.90 0.95 ND U 10.0 1.90 0.95 0 ND U 10.0 1.90 0.95

Benzene 5 170 U 1.0 0.32 0.16 ND U 1.0 0.32 0.16 0 ND U 1.0 0.32 0.16

Bromodichloromethane 0.12 50,000 U 1.0b 0.28 0.14 ND U 1.0b 0.28 0.14 0 ND U 1.0b 0.28 0.14

Bromoform 80 510 U 1.0 0.28 0.14 ND U 1.0 0.28 0.14 0 ND U 1.0 0.28 0.14

Bromomethane 8.7 50,000 U 2.0 0.48 0.24 ND U 2.0 0.48 0.24 0 ND U 2.0 0.48 0.24

Carbon Tetrachloride 5 520 U 1.0 0.20 0.10 ND U 1.0 0.20 0.10 0 ND U 1.0 0.20 0.10

Chlorobenzene 100 50 U 1.0 0.42 0.21 ND U 1.0 0.42 0.21 0 ND U 1.0 0.42 0.21

Chloroethane 21,000 16 U 1.0 0.42 0.21 ND U 1.0 0.42 0.21 0 ND U 1.0 0.42 0.21

Chloroform 70 2,400 U 1.0 0.14 0.07 ND U 1.0 0.14 0.07 0 ND U 1.0 0.14 0.07

Chloromethane 1.8 50,000 U 1.0 0.84 0.42 ND U 1.0 0.84 0.42 0 ND U 1.0 0.84 0.42

cis-1,2-Dichloroethylene (cis1,2-Dichloroethene) 70 50,000 U 1.0 0.32 0.16 ND U 1.0 0.32 0.16 0 ND U 1.0 0.32 0.16

Dibromochloromethane 

(Chlorodibromomethane) 0.16 50,000 U 1.0b 0.38 0.19 ND U 1.0b 0.38 0.19 0 ND U 1.0b 0.38 0.19

Ethylbenzene 700 30 U 1.0 0.46 0.23 ND U 1.0 0.46 0.23 0 ND U 1.0 0.46 0.23

Hexachlorobutadiene 0.86 6 U 1.0b 0.38 0.19 ND U 1.0b 0.38 0.19 0 ND U 1.0 0.38 0.19

Methyl ethyl ketone 

(2-Butanone) 7,100 8,400 U 10.0 1.20 0.60 ND U 10.0 1.20 0.60 0 ND U 10.0 1.20 0.60

Methyl isobutyl ketone 

(4-Methyl-2-pentanone) 2,000 1,300 U 10.0 3.80 1.90 ND U 10.0 3.80 1.90 0 ND U 10.0 3.80 1.90

Methyl tert-butyl Ether 12 5 U 1.0 0.52 0.26 ND U 1.0 0.52 0.26 0 ND U 1.0 0.52 0.26

Methylene chloride 4.8 9,100 U 5.0b 0.70 0.35 ND U 5.0b 0.70 0.35 0 ND U 5.0 0.70 0.35

Styrene 100 10 U 1.0 0.50 0.25 ND U 1.0 0.50 0.25 0 ND U 1.0 0.50 0.25

Tetrachloroethane, 1,1,1,2- 0.52 50,000 U 1.0b 0.26 0.13 ND U 1.0b 0.26 0.13 0 ND U 1.0 0.26 0.13

Tetrachloroethane, 1,1,2,2- 0.067 500 U 1.0b 0.20 0.10 ND U 1.0b 0.20 0.10 0 ND U 1.0b 0.20 0.10

Tetrachloroethylene 

(Tetrachloroethene) 5 170 U 1.0 0.48 0.24 ND U 1.0 0.48 0.24 0 ND U 1.0 0.48 0.24

Toluene 1,000 40 U 1.0 0.34 0.17 ND U 1.0 0.34 0.17 0 ND U 1.0 0.34 0.17

trans-1,2-Dichloroethylene 

(trans-1,2-Dichloroethene) 100 260 U 1.0 0.38 0.19 ND U 1.0 0.38 0.19 0 ND U 1.0 0.38 0.19

Trichloroethylene 

(Trichloroethene) 5 310 U 1.0 0.32 0.16 ND U 1.0 0.32 0.16 0 ND U 1.0 0.32 0.16

Vinyl chloride 2 3,400 U 1.0 0.46 0.23 ND U 1.0 0.46 0.23 0 ND U 1.0 0.46 0.23

Xylenes 10,000 20 U 1.0 0.38 0.19 ND U 1.0 0.38 0.19 0 ND U 1.0 0.38 0.19

EPA 6020 Lead 15 5000 0.17 J 0.5 0.22 0.11 0.21 J 0.5 0.22 0.11 21.1 -- -- -- -- --

Notes:

dup - duplicate

GRO - gasoline range organics

LOD - limit of detection

LOQ - limit of quantitation or reporting limit (RL)

PAHs - polycyclic aromatic hydrocarbons

RPD - relative percent difference

TPH - total petroleum hydrocarbons

VOC - volatile organic compound

-- not analyzed

Bold - Result exceeds one or both DOH EALs

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

a DOH EALs (DOH, 2009): Table D-1b. Groundwater Action Levels (Groundwater is a current or potential drinking water resource; surface water body is not located within 150 meters of release site).

b In the case where an EAL for a specific chemical is less than the LOQ for a commercial laboratory, it is generally acceptable to consider the LOQ in place of the action level (DOH, Evaluation of Environmental 

All units are in micrograms per liter (μg/L).

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

ND

U - Indicates the compound or analyte was analyzed for, but not detected. The result is reported as ND. 

Hazards at Sites with Contaminated Soil and Groundwater 2008, updated March 2009). 

J - Estimated result. Indicates that the compound was identified, but the concentration was above the DL and below the LOQ.

DRO - diesel range organics

DL - detection limit or method detection limit (MDL)

Trip Blank - (7/19/2012)

ES086

RPD 

Duplicate 

(%)

RHMW05

ES079

Result Result

RHMW05

EPA 8270D SIM (PAHs)

EPA 8260B (VOCs)

ES080

DOH Groundwater 

Gross 

Contamination 

EALsa 

Method Chemical

DOH Drinking 

Water EALs for 

Human 

Toxicitya 

ND ND

ND

ND

ND

ND

ND

ND

ND

Table 3-3: Historical and Current Groundwater Sample Analytical Results, August 2009 through July 2012

Result Q LOQ LOD DL Result Q LOQ LOD DL Result Q LOQ LOD DL Result Q 

August 2009 ND U 457 NA 171 ND U 100 NA 30 -- -- -- NA -- -- -- October 2009 ND U 444 NA 167 ND U 100 NA 30 ND U 494 NA 185 ND U January 2010 1,490 440 NA 165 ND U 100 NA 30 322 J 460 NA 172 ND U 

April 2010 288 J 471 NA 176 ND U 100 NA 30 ND U 471 NA 176 ND U 

July 2010 -- -- -- -- -- -- -- -- -- -- ND U 426 -- 160 ND U October 2010 ND U 150 80.8 40.4 ND U 20.0 12.1 6.06 ND U 150 80.8 40.4 ND U January 2011 ND U 150 80.8 40.4 ND U 20.0 12.1 6.06 ND U 150 80.8 40.4 ND U April 2011 ND U 150 80.8 40.4 ND U 20.0 12.1 6.06 ND U 150 80.8 40.4 ND U July 2011 ND U 150 80.8 40.4 ND U 20.0 12.1 6.06 ND U 150 80.8 40.4 ND U October 2011 ND U 150 80.8 40.4 ND U 20.0 12.1 6.06 ND U 150 80.8 40.4 ND U January 2012 ND U 150 80.8 40.4 ND U 20.0 12.1 6.06 ND U 150 80.8 40.4 ND U April 2012 220 ++ 150 80.8 40.4 ND U 20.0 12.1 6.06 160 ++ 150 80.8 40.4 ND U 

July 2012 ND U 150 80.8 40.4 ND U 20.0 12.1 6.06 ND U 150 80.8 40.4 ND U Notes:++ - Analyst noted that the chromatogram of this sample is mainly non-diesel hydrocarbons within the boiling point range of diesel fuel.DOH Drinking Water EALs for Human Toxicity a : TPH-DRO = 210 μg/L; TPH-GRO = 100 μg/L

DOH Groundwater Gross Contamination EALs a : TPH-DRO = 100 μg/L; TPH-GRO = 100 μg/L

a DOH EALs (DOH, 2009): Table D-1b. Groundwater Action Levels (Groundwater is a current or potential drinking water resource; surface water body

TPH-DRO TPH-GRO 

OWDFMW01 HDMW2253-03

TPH-DRO TP

Bold - Result exceeds one or both DOH EALs-- The monitoring well was not sampled. is not located within 150 meters of release site).All units are in micrograms per liter (μg/L)U - Indicates that the compound was analyzed for, but not detected. The result is reported as ND.ND - not detected Q - data qualifierJ - Estimated result. Indicates that the compound was identified, but the concentration was above the DL and below the LOQ.DL - detection limit or method detection limit (MDL)LOQ - limit of quantitation or reporting limit (RL)

NA - not available

LOD - limit of detection 

Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 4 

Summary, Conclusions, and Recommendations 

September 2012

4-1

Section 4 Summary, Conclusions, and 

Recommendations

4.1 Summary

Benzene was detected at a concentration of 1.3 μg/L in monitoring well OWDFMW01, which is 

below the DOH Drinking Water and Groundwater Gross Contamination EALs. Acetone was 

detected at an estimated concentration of 2.3 μg/L in monitoring well OWDFMW01, which is 

below the DOH Drinking Water and Gross Contamination EALs. 2-Butanone was detected at an

estimated concentration of 1.0 μg/L in monitoring well OWDFMW01, which is below the DOH 

Drinking Water and Groundwater Gross Contamination EALs. No other COPCs were detected 

at or above the LODs or the LOQs in monitoring wells HDMW2253-03 and OWDFMW01 

during the July 2012 monitoring event.

4.2 Conclusions

Concentrations of PAHs and VOCs were previously not detected above the EALs in the August 

2009, October 2009, January 2010, April 2010, July 2010, October 2010, January 2011, April 

2011, July 2011, October 2011, January 2012, and April 2012 groundwater monitoring events. 

PAHs and VOCs were also not detected above the EALs during the July 2012 monitoring event. 

The data continues to suggest that historically, TPH-DRO was the only COPC present in any 

notable quantity for the site.

TPH-DRO concentrations in OWDFMW01 significantly decreased from January 2010 (1,490 

μg/L) to April 2010 (288 μg/L) and were not detected in the subsequent six monitoring events 

(Table 3-3). The concentrations of TPH-DRO at HDMW2253-03 decreased from 322 μg/L in 

January 2010 to non-detectable levels for the eight consecutive quarterly monitoring events from 

April 2010 to January 2012. In the April 2012 monitoring event, the TPH-DRO concentration 

from OWDFMW01 increased to a level above the DOH Drinking Water EAL. TPH-DRO 

concentration in HDMW2253-03 also increased but to a level below the DOH Drinking Water 

EAL. However, the elevated concentrations were mainly due to non-diesel hydrocarbons 

detected by the analytical method. MADEP EPH analytical results in the October 2011 

monitoring event indicated that the detected hydrocarbons were most likely from non-petroleum 

sources. The true TPH-DRO concentrations of the samples were likely lower, but were reported 

at higher concentrations as a result of non-diesel hydrocarbons detected by the analytical method. 

TPH-DRO concentrations at both HDMW2253-03 and OWDFMW01 decreased to 

non-detectable levels during the July 2012 monitoring event. The data suggests TPH-DRO 

concentrations detected in the facility are not impacting the two outside monitoring wells.

The October 2010 detection of acetone at an estimated concentration below the DOH Drinking 

Water EAL was the first at monitoring well OWDFMW01. Acetone was also detected at an 

estimated concentration in the trip blank sample in October 2010. Acetone was not detected in 

the subsequent five monitoring events. This strongly suggested that acetone was introduced to 

the samples during transport to and from the laboratory. In the April 2012 and July 2012 

monitoring events, acetone was again detected at estimated concentrations in monitoring well 
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 4 

Summary, Conclusions, and Recommendations 

September 2012

4-2

OWDFMW01 below the DOH Drinking Water EAL. None of the trip blanks for the April 2012 

and July 2012 monitoring events contained traces of the analyte, indicating that acetone was 

present at very low levels in the groundwater.

The October 2010 detections of lead at concentrations below the DOH Drinking Water EAL 

were the first at these two monitoring wells (OWDFMW01 and HDMW2253-03). Lead was not 

detected in any samples in the January 2011 monitoring event or in the April 2011 monitoring 

event. Lead was detected at estimated concentrations below the DOH Drinking Water EAL at 

both monitoring wells in the July 2011 monitoring event. Lead was detected in monitoring well 

HDMW2253-03 at a concentration below the DOH Drinking Water EAL and in monitoring well 

OWDFMW01 at an estimated concentration below the DOH Drinking Water EAL in the 

October 2011 monitoring event. Lead was detected in monitoring wells OWDFMW01 and 

HDMW2253-03 at estimated concentrations below the DOH Drinking Water EAL in the January 

2012 monitoring event. Lead was detected in monitoring well HDMW2253-03 below the DOH 

Drinking Water EAL in the April 2012 monitoring event. Lead was not detected in monitoring 

wells OWDFMW01 and HDMW2253-03 during the July 2012 monitoring event. Lead 

concentrations in both monitoring wells have fluctuated at very low levels below the DOH 

Drinking Water EAL.

The January 2011 detection of benzene at an estimated concentration below the DOH Drinking 

Water EAL in OWDFMW01 was the first at this monitoring well. Benzene was detected at an 

estimated concentration in the duplicate sample collected from OWDFMW01 in April 2011; 

however, it was not detected in the July 2011 and October 2011 monitoring events. It was 

detected at an estimated concentration below the DOH Drinking Water EAL in HDMW2253-03 

in the October 2011 monitoring event. Benzene was detected at an estimated concentration in 

monitoring well OWDFMW01 in the January 2012 monitoring event, which was below the DOH 

Drinking Water EAL. Benzene was detected at estimated concentrations below the DOH 

Drinking Water EAL at monitoring wells OWDFMW01 and HDMW2253-03 in the April 2012 

monitoring event. Benzene was detected at a concentration below the DOH Drinking Water 

EAL at monitoring well OWDFMW01, during the July 2012 monitoring event. Benzene was not 

detected at monitoring well HDMW2253-03, during the July 2012 monitoring event. Benzene 

concentrations have fluctuated in both monitoring wells at very low levels below the DOH 

Drinking Water EAL.

The April 2011 detections of xylenes and toluene in OWDFMW01 were the first at these 

monitoring wells. Xylenes and toluene were not detected in the July 2011, October 2011, 

January 2012, April 2012, and July 2012 monitoring events. Xylene and toluene concentrations 

have exhibited no trends, and the April 2011 detections of both analytes were very low to be of 

concern relative the DOH Drinking Water EALs.

The July 2012 detection of 2-butanone in OWDFMW01 was the first at this monitoring well. 

2-Butanone was detected at an estimated concentration that was very low to be of concern 

relative to the DOH Drinking Water EAL.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 4 

Summary, Conclusions, and Recommendations 

September 2012

4-3

4.3 Recommendations

No COPCs were detected above the DOH Drinking Water EALs during the July 2012 

monitoring event. The data suggest that COPC concentrations detected in the facility are not 

impacting the two outside monitoring wells. It is recommended that quarterly sampling remain 

the same and attention continue to be paid to concentration levels at both monitoring wells for 

signs of contaminant migration.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 4 

Summary, Conclusions, and Recommendations 

September 2012

4-4

This page is intentionally left blank.
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 5

References

September 2012

5-1

Section 5 References

AMEC Earth and Environmental, Inc., 2002. Red Hill Bulk Fuel Storage Facility Investigation 

Report, Prepared for NAVFAC Pacific. August.

Dawson Group, Inc., 2006. Fourth Quarter 2005 Groundwater Sampling Report, Red Hill Fuel 

Storage Facility, Hawaii. February. 

DOH, 2009. Evaluation of Environmental Hazards at Sites with Contaminated Soil and 

Groundwater. Updated March 2009.

DON, 2007. Project Procedures Manual, U.S. Navy Environmental Restoration Program, 

NAVFAC Pacific. February.

Earth Tech, Inc, 2000. Remedial Investigation Phase II, Volume I, Technical Report, Red Hill 

Oily Waste Disposal Facility, Halawa, Oahu, Hawaii. September.

Environet, 2010. Work Plan, Long-Term Monitoring, Red Hill Bulk Fuel Storage Facility, Pearl 

Harbor, O‘ahu, Hawai‘i. September.

Hawai‘i Administrative Rules, Title 11, Chapter 281, Subchapter 7.

TEC, 2006. Red Hill Bulk Fuel Storage Facility, Final - Addendum Planning Documents, Pearl 

Harbor, Hawaii. May.

_____, 2008. Red Hill Bulk Fuel Storage Facility, Final Groundwater Protection Plan, Pearl 

Harbor, Hawaii. January 2008 revised in December 2009.

U.S. Geological Survey (USGS), 2005. Aerial Image. http://hawaii.wr.usgs.gov/index.html.

 
Quarterly Groundwater Monitoring Report – Outside (Non-Tunnel) Wells 

Red Hill Bulk Fuel Storage Facility, JBPHH, O‘ahu, Hawai‘i

Section 5

References

September 2012

5-2

This page is intentionally left blank.
Appendix A

DOH Correspondence





Appendix B

Field Notebook



Appendix C

Groundwater Sampling Logs

WELL ID: LOCATION: PROJECT NO:

INITIAL WATER LEVEL: DATE: TIME:

TOTAL DEPTH OF WELL: PERSONNEL INVOLVED:

LENGTH OF SATURATED ZONE: WEATHER CONDITIONS:

VOLUME OF WATER TO BE REMOVED: METHOD OF REMOVAL:

WATER LEVEL AFTER PURGING: PUMPING RATE: 

WELL PURGE DATA:

TIME VOLUME 

REMOVED pH COND 

(mS/cm)

TURBIDITY 

(NTU) DO (mg/l) TEMP (o

C) SALINITY 

(ppt)

REDOX (ORP) 

(mV)

1104 3 L 5.17 0.000 43.7 6.68 25.83 0.0 80

1108 6 L 6.29 0.598 39.7 6.19 24.07 0.1 5

1112 9 L 6.30 0.601 39.6 3.79 23.48 0.1 -15

SAMPLE RETRIEVAL METHOD: APPEARANCE OF SAMPLE: 

COLOR Brown

SAMPLE ID: TURBIDITY Low

SAMPLE COLLECTION TIME: SEDIMENT None

SAMPLED BY: OTHER None

COMMENTS AND OBSERVATIONS:

LABORATORY ANALYSIS PARAMETERS AND PRESERVATIVES: TPH-GRO (EPA 8260B) & VOCs (EPA 8260B) with no preservative

TPH-DRO (EPA8015B) & PAHs (EPA 8270C SIM) with no preservative, and dissolved lead (EPA 6020) with nitric acid preservative

NUMBER AND TYPES OF SAMPLE CONTAINERS FILLED:

 

DECONTAMINATION PROCEDURES:

SAMPLES DELIVERED TO: TRANSPORTERS:

SAMPLE DELIVERY DATE: SAMPLE DELIVERY TIME:

CAPACITY OF CASING (GALLONS/LINEAR FOOT)

2"-0.16; 4"-0.65; 6"-1.47; 8"-2.61; 10"-4.08; 12"-5.87

GROUNDWATER SAMPLING LOG

HDMW2253-03 Red Hill Bulk Fuel Storage Facility 1022-024

207.87 feet bTOC (944 DLNR) 7/19/2012 1101

1,575 feet bTOC MS, JT

N/A Sunny

N/A Bailer

7/19/2012 1438

N/A 0.82 L/min

 Bailer

ES083

1130

MS, JT

(3) - 40 mL VOAs, (4) - 1 L amber bottle, (1) - 500 mL polyethylene bottle

Alconox, triple rinse with distilled water

APPL, INC., via FedEx MS, JT

WELL ID: LOCATION: PROJECT NO:

INITIAL WATER LEVEL: DATE: TIME:

TOTAL DEPTH OF WELL: PERSONNEL INVOLVED:

LENGTH OF SATURATED ZONE: WEATHER CONDITIONS:

VOLUME OF WATER TO BE REMOVED: METHOD OF REMOVAL:

WATER LEVEL AFTER PURGING: PUMPING RATE: 

WELL PURGE DATA:

TIME VOLUME 

REMOVED pH COND 

(mS/cm)

TURBIDITY 

(NTU) DO (mg/l) TEMP (o

C) SALINITY 

(%)

REDOX (ORP) 

(mV)

1230 4 L 10.94 3.20 0.0 6.89 30.61 1.1 -83

1235 8 L 11.01 3.32 0.0 5.75 28.41 1.2 -87

1240 12 L 11.08 3.45 0.0 5.62 28.00 1.2 -85

SAMPLE RETRIEVAL METHOD: APPEARANCE OF SAMPLE: 

COLOR Clear

SAMPLE ID: TURBIDITY None

SAMPLE COLLECTION TIME: SEDIMENT None

SAMPLED BY: OTHER None

COMMENTS AND OBSERVATIONS:

LABORATORY ANALYSIS PARAMETERS AND PRESERVATIVES: TPH-GRO (EPA 8260B) & VOCs (EPA 8260B) with no preservative

TPH-DRO (EPA8015B) & PAHs (EPA 8270C SIM) with no preservative, and dissolved lead (EPA 6020) with nitric acid preservative

NUMBER AND TYPES OF SAMPLE CONTAINERS FILLED:

DECONTAMINATION PROCEDURES:

SAMPLES DELIVERED TO: TRANSPORTERS:

SAMPLE DELIVERY DATE: SAMPLE DELIVERY TIME:

CAPACITY OF CASING (GALLONS/LINEAR FOOT)

2"-0.16; 4"-0.65; 6"-1.47; 8"-2.61; 10"-4.08; 12"-5.87

7/19/2012 1438

N/A 0.6 L/min

Bailer

ES084 MS/MSD

1300

MS, JT

Primary: (3) - 40 mL VOAs, (4) - 1 L amber bottle, (1) - 500 mL polyethylene bottle,

MS/MSD: (3) - 40 mL VOAs, (4) - 1 L amber bottle, (1) - mL polyethylene bottle

Alconox, triple rinse with distilled water

APPL, INC., via FedEx MS, JT

142.8 feet bTOC MS, JT

22.65 feet Sunny

N/A Bailer

GROUNDWATER SAMPLING LOG

OWDFMW01 Red Hill Bulk Fuel Storage Facility 1022-024

120.15 feet bTOC 7/19/2012 1220

Appendix D

Laboratory Analytical Results,

July 2012 (on CD-ROM)