**Appendix B - Summary of Changes to Fuel Assumptions with Emissions Testing Data**

**FacilityID CombustorID_common**  **Data Source Fuel**  **Fuel Source Comments**  **Revisions Needed?**
GAGPMadisonPly 800 Wood Waste Boiler ICR Phase II - Comments Wood: Bark Assumed to be as listed in ICR Phase I No fuel information provided with comments (EPA-HQ-OAR-2002- 0058-2745.1); Assuming fuel information from ICR Phase II Templates. Fuel source changed to, "As listed in ICR Phase II Template". GAGPMadisonPly 800 Wood Waste Boiler ICR Phase II - ERT Wood: Bark/Wood: Plywood, Particleboard (containing glues or resins) Assumed to be as listed in Phase II ERG Fuel Analysis Template ICR Phase II Template data shows bark as only fuel. Fuel type changed to bark only.
MENewPage-Rumford Cogen#6 ICR Phase II - ERT /Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ Assumed to be as listed in Phase II ERG Fuel Analysis Template ICR Phase II Template shows these fuels, so the fuel assumption is correct. Fuel source changed to, "As listed in ICR Phase II Template".
MENewPage-Rumford Cogen#7 ICR Phase II - ERT /Biomass/Coal: Bituminous/Industrial Sludge/Noncondensable Gas (includes stripper offgas)/Tire Derived Fuel (TDF)/ Assumed to be as listed in Phase II ERG Fuel Analysis Template ICR Phase II Template shows these fuels, so the fuel assumption is correct. Fuel source changed to, "As listed in ICR Phase II Template".

SCSonocoHartsville Boiler Number 9 ICR Phase II - ERT /Coal: Bituminous/ Assumed to be as listed in Phase I ERT attachment with operating data shows bituminous coal, boiler ash, paper & paper residues, and biomass as fuel inputs. Fuel type changed to represent the fuels specified in the ERT attachment.

SCSonocoHartsville Boiler Number 9 ICR Phase II - Test Report /Coal: Bituminous/ Assumed to be as listed in Phase I ERT attachment with operating data shows bituminous coal, boiler ash, paper & paper residues, and biomass as fuel inputs. Fuel type changed to represent the fuels specified in the ERT attachment.

SCSonocoHartsville Boiler Number 9 ICR Phase II - Voluntary /Coal: Bituminous/ Assumed to be as listed in Phase I ERT attachment with operating data shows bituminous coal, boiler ash, paper & paper residues, and biomass as fuel inputs. Fuel type changed to represent the fuels specified in the ERT attachment.
TNMilanArmyAmmunitionPlant D88L-1, Source #27-0010-86 ICR Phase II - ERT No. 2 Distillate Assumed to be as listed in Phase II ERG Fuel Analysis Template ICR Phase II Template data shows #2 distillate oil as only fuel. Fuel type changed to #2 distillate oil only; fuel source changed to, "As listed in ICR Phase II Template".**Appendix C - Summary of Changes to Current Control Configurations on Major Source Boilers and Process Heaters**

FacilityID UnitID Major Source?Classification Design Capacity (MMBtu/hr)Fuel Category

for Unit Previous Control

Configuration Corrected Control Configuration (Currently Installed on Unit) Reason for Change ILADMPeoria EU-PH113 Major SourceBoiler 382Gas 1 Electrostatic Precipitator No HAP APCD Control Review of controls shows that this unit does not have an ESP

KYMoreheadStateUniv 02 Major SourceBoiler 87.4Coal Fabric Filter Cyclone or Multiclone Review of controls shows that only 20% of vent gas is diverted through FF, so the majority of control for this unit is it's multiclone MEMadisonPaper #4 Boiler ME5949 Major SourceBoiler 119Heavy Liquid Spray Dryer No HAP APCD Control Review of controls shows that this unit does not have a spray dryer MEMadisonPaper #6 Boiler ME6454 Major SourceBoiler 99Heavy Liquid Spray Dryer No HAP APCD Control Review of controls shows that this unit does not have a spray dryer
MNVersoPaper EU015 Wickes Major SourceBoiler 135Gas 1 No HAP APCD Control Cyclone or Multiclone Review of controls shows that unit actually has multiclone installed instead of no equipment MOAnheuserBusch Boiler7 Major SourceBoiler 232Gas 1 Electrostatic Precipitator No HAP APCD Control Review of controls shows this unit does not have an ESP SCINVISTACamdenPlant Unit ID 8 - Vaporizer No. 3 Major SourceProcess Heater 43Heavy Liquid Fabric Filter No HAP APCD Control Review of controls shows that this unit does not have a FF installed SCINVISTACamdenPlant Unit ID 9 - Vaporizer No. 4 Major SourceProcess Heater 43Heavy Liquid Fabric Filter No HAP APCD Control Review of controls shows that this unit does not have a FF installed

WASierraPacific Co-Gen Major SourceBoiler 287.5Wet BiomassNo HAP APCD Control Electrostatic Precipitator/Over-fire Air Review of controls shows this unit actually has an ESP and over-fire air installed instead of no equipment