### 13339 Hagers Ferry Road Huntersville, NC 28078-7929 McGuire Nuclear Complex - MG03A2 Phone: 980-875-5245 Fax: 980-875-4349 

# Order Summary Report Analytical Laboratory

Order Number: J11030112

Lab Contact: Jason C Perkins


### Date: 3/23/2011 Customer Address: 253 Plant Allen Road Customer Name(s): Don Scruggs, Robbin Jolly, Ray Lidke, Bill Kennedy

Belmont, NC 28012

Phone: 980-875-5348
Report Authorized By: (Signature)



### Program Comments: Test Burn #3 - Day 2
Data Flags & Calculations: Any analytical tests or individual analytes within a test flagged with an "X" or "1" indicate a deviation from the method quality system or quality control requirement. All results are reported on a dry weight basis unless otherwise noted. Data Package: This data package includes analytical results that are applicable only to the samples described in this narrative. An estimation of the uncertainty of measurement for the results in the report is available upon request. This report shall not be reproduced, except in full, without the written consent of the Analytical Laboratory. Please contact the Analytical laboratory with any questions. The order of individual sections within this report is as follows: Job Summary Report, Sample Identification, Technical Validation of Data Package, Analytical Laboratory Certificate of Analysis, Analytical Laboratory QC Reports, Sub-contracted Laboratory Results, Customer Specific Data Sheets, Reports & Documentation, Customer Database Entries, Test Case Narratives, Chain of Custody (COC)
Certification: The Analytical Laboratory holds the following State Certifications : North Carolina (DENR) Certificate #248, South Carolina (DHEC) Laboratory ID # 99005. Contact the Analytical Laboratory for definitive information about the certification status of specific methods.

## Sample ID's & Descriptions:

Sample ID Plant/Station Collection Date and Time Collected By Sample Description 2011005054 ALLEN 03-Mar-11 9:13 AM Jeremy D. FGD Purge Eff 2011005055 ALLEN 03-Mar-11 8:47 AM Jeff Womack EQ Tank Eff 2011005056 ALLEN 03-Mar-11 8:44 AM Jeff Womack BioReactor 1 Inf 2011005057 ALLEN 03-Mar-11 8:45 AM Jeremy D. BioReactor 2 Inf 2011005058 ALLEN 03-Mar-11 8:50 AM Jeff Womack BioReactor 2 Eff 2011005059 ALLEN 03-Mar-11 11:05 AM DANIEL HUDDLESTON Hg Blk BioReactor 1 Inf 2011005060 ALLEN 03-Mar-11 11:15 AM DANIEL HUDDLESTON Hg Blk BioReactor 2 Inf 2011005061 ALLEN 03-Mar-11 11:10 AM DANIEL HUDDLESTON Hg Blk BioReactor 2 Eff 2011005062 ALLEN 03-Mar-11 10:55 AM Jeff Womack Filter Blk 9 Total Samples

### COC and .pdf report are in agreement with sample totals

and analyses (compliance programs and procedures). All Results are less than the laboratory reporting limits. All laboratory QA/QC requirements are acceptable. The Vendor Laboratories have been qualified by the Analytical Laboratory Yes No



# Technical Validation Review C hecklist:

Yes No

Yes No



## Report Sections Included:

Job Summary Report Sub-contracted Laboratory Results Sample Identification Customer Specific Data Sheets, Reports, & Documentation Technical Validation of Data Package Customer Database Entries Analytical Laboratory Certificate of Analysis Test Case Narratives Analytical Laboratory QC Report Chain of Custody

Reviewed By: 

### DataBase Administrator Date: 

### 3/23/2011 Yes

Electronic Data Deliverable (EDD) Sent Separately

# Certificate of Laboratory Analysis This report shall not be reproduced, except in full.



### Order # J11030112

2011005054 Collection Date: 03-Mar-11 9:13 AM 

### Site: FGD Purge Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY (COLD VAPOR) IN WATER Mercury (Hg) 56.6 ug/L EPA 245.1 17-Mar-11 10:29 2.5 MHH7131 Mercury Dissolved (cold vapor) in Water (Filtered) Mercury (Hg) 22.7 ug/L EPA 245.1 17-Mar-11 10:32 1 MHH7131
TOTAL RECOVERABLE METALS BY ICP Boron (B) 88.0 mg/L EPA 200.7 14-Mar-11 13:15 0.5 DJSULL1
DISSOLVED METALS BY ICP-MS Selenium (Se) 1260 ug/L EPA 200.8 11-Mar-11 10:55 10 KRICHAR
TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) 147 ug/L EPA 200.8 14-Mar-11 14:05 10 KRICHAR Chromium (Cr) 136 ug/L EPA 200.8 14-Mar-11 14:05 10 KRICHAR Copper (Cu) 208 ug/L EPA 200.8 14-Mar-11 14:05 10 KRICHAR Nickel (Ni) 290 ug/L EPA 200.8 14-Mar-11 14:05 10 KRICHAR Selenium (Se) 1500 ug/L EPA 200.8 14-Mar-11 14:05 10 KRICHAR Silver (Ag) < 10 ug/L EPA 200.8 14-Mar-11 14:05 10 KRICHAR Zinc (Zn) 348 ug/L EPA 200.8 14-Mar-11 14:05 20 KRICHAR
SELENIUM SPECIATION Vendor Parameter Complete V_AS&C 

### 2011005055 Collection Date: 03-Mar-11 8:47 AM 

### Site: EQ Tank Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY (COLD VAPOR) IN WATER Mercury (Hg) 47.9 ug/L EPA 245.1 17-Mar-11 10:34 2.5 MHH7131
TOTAL RECOVERABLE METALS BY ICP Boron (B) 70.2 mg/L EPA 200.7 14-Mar-11 13:19 0.5 DJSULL1
DISSOLVED METALS BY ICP-MS Selenium (Se) 1020 ug/L EPA 200.8 11-Mar-11 10:59 10 KRICHAR
TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) 241 ug/L EPA 200.8 14-Mar-11 14:00 10 KRICHAR Chromium (Cr) 261 ug/L EPA 200.8 14-Mar-11 14:00 10 KRICHAR Copper (Cu) 339 ug/L EPA 200.8 14-Mar-11 14:00 10 KRICHAR Nickel (Ni) 430 ug/L EPA 200.8 14-Mar-11 14:00 10 KRICHAR Selenium (Se) 2520 ug/L EPA 200.8 14-Mar-11 14:00 10 KRICHAR

# Certificate of Laboratory Analysis This report shall not be reproduced, except in full.



### Order # J11030112

2011005055 Collection Date: 03-Mar-11 8:47 AM 

### Site: EQ Tank Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst TOTAL RECOVERABLE METALS BY ICP-MS Silver (Ag) < 10 ug/L EPA 200.8 14-Mar-11 14:00 10 KRICHAR Zinc (Zn) 464 ug/L EPA 200.8 14-Mar-11 14:00 20 KRICHAR 

### 2011005056 Collection Date: 03-Mar-11 8:44 AM 

### Site: BioReactor 1 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY 1631 Vendor Parameter Complete V_BRAND
TOTAL RECOVERABLE METALS BY ICP Boron (B) 46.7 mg/L EPA 200.7 14-Mar-11 13:23 0.5 DJSULL1
DISSOLVED METALS BY ICP-MS Selenium (Se) 905 ug/L EPA 200.8 11-Mar-11 11:03 10 KRICHAR
TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) < 10 ug/L EPA 200.8 14-Mar-11 13:55 10 KRICHAR Chromium (Cr) < 10 ug/L EPA 200.8 14-Mar-11 13:55 10 KRICHAR Copper (Cu) < 10 ug/L EPA 200.8 14-Mar-11 13:55 10 KRICHAR Nickel (Ni) 14.8 ug/L EPA 200.8 14-Mar-11 13:55 10 KRICHAR Selenium (Se) 970 ug/L EPA 200.8 14-Mar-11 13:55 10 KRICHAR Silver (Ag) < 10 ug/L EPA 200.8 14-Mar-11 13:55 10 KRICHAR Zinc (Zn) < 20 ug/L EPA 200.8 14-Mar-11 13:55 20 KRICHAR
SELENIUM SPECIATION Vendor Parameter Complete V_AS&C 

### 2011005057 Collection Date: 03-Mar-11 8:45 AM 

### Site: BioReactor 2 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY 1631 Vendor Parameter Complete V_BRAND
TOTAL RECOVERABLE METALS BY ICP Boron (B) 48.8 mg/L EPA 200.7 14-Mar-11 13:27 0.5 DJSULL1
TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) < 10 ug/L EPA 200.8 14-Mar-11 13:50 10 KRICHAR Chromium (Cr) < 10 ug/L EPA 200.8 14-Mar-11 13:50 10 KRICHAR Copper (Cu) < 10 ug/L EPA 200.8 14-Mar-11 13:50 10 KRICHAR Nickel (Ni) 11.8 ug/L EPA 200.8 14-Mar-11 13:50 10 KRICHAR

# Certificate of Laboratory Analysis This report shall not be reproduced, except in full.



### Order # J11030112

2011005057 Collection Date: 03-Mar-11 8:45 AM 

### Site: BioReactor 2 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst TOTAL RECOVERABLE METALS BY ICP-MS Selenium (Se) < 10 ug/L EPA 200.8 14-Mar-11 13:50 10 KRICHAR Silver (Ag) < 10 ug/L EPA 200.8 14-Mar-11 13:50 10 KRICHAR Zinc (Zn) < 20 ug/L EPA 200.8 14-Mar-11 13:50 20 KRICHAR
SELENIUM SPECIATION Vendor Parameter Complete V_AS&C 

### 2011005058 Collection Date: 03-Mar-11 8:50 AM 

### Site: BioReactor 2 Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY 1631 Vendor Parameter Complete V_BRAND
TOTAL RECOVERABLE METALS BY ICP Boron (B) 55.6 mg/L EPA 200.7 14-Mar-11 13:31 0.5 DJSULL1
TOTAL RECOVERABLE METALS BY ICP-MS Arsenic (As) < 5 ug/L EPA 200.8 14-Mar-11 13:45 5 KRICHAR Chromium (Cr) < 5 ug/L EPA 200.8 14-Mar-11 13:45 5 KRICHAR Copper (Cu) < 5 ug/L EPA 200.8 14-Mar-11 13:45 5 KRICHAR Nickel (Ni) < 5 ug/L EPA 200.8 14-Mar-11 13:45 5 KRICHAR Selenium (Se) < 5 ug/L EPA 200.8 14-Mar-11 13:45 5 KRICHAR Silver (Ag) < 5 ug/L EPA 200.8 14-Mar-11 13:45 5 KRICHAR Zinc (Zn) < 10 ug/L EPA 200.8 14-Mar-11 13:45 10 KRICHAR
SELENIUM SPECIATION Vendor Parameter Complete V_AS&C 

### 2011005059 Collection Date: 03-Mar-11 11:05 AM 

### Site: Hg Blk BioReactor 1 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY 1631 Vendor Parameter Complete V_BRAND 

### 2011005060 Collection Date: 03-Mar-11 11:15 AM 

### Site: Hg Blk BioReactor 2 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY 1631

# Certificate of Laboratory Analysis This report shall not be reproduced, except in full.



### Order # J11030112

2011005060 Collection Date: 03-Mar-11 11:15 AM 

### Site: Hg Blk BioReactor 2 Inf Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY 1631 Vendor Parameter Complete V_BRAND 

### 2011005061 Collection Date: 03-Mar-11 11:10 AM 

### Site: Hg Blk BioReactor 2 Eff Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst MERCURY 1631 Vendor Parameter Complete V_BRAND 

### 2011005062 Collection Date: 03-Mar-11 10:55 AM 

### Site: Filter Blk Matrix: OTHER

Analyte Analysis Date/Time Method Units Qualifiers RDL Result 

### Sample #:

Analyst DISSOLVED METALS BY ICP-MS Selenium (Se) < 2 ug/L EPA 200.8 11-Mar-11 11:06 2 KRICHAR

## March 21, 2011 Jay Perkins Duke Energy Analytical Laboratory Mail Code MGO3A2 (Building 7405) 13339 Hagers Ferry Rd. Huntersville, NC 28078 (704) 875-5245 Project: Allen – FGD Alternative Fuels Test Burn #3 - Daily) (LIMS # J11030112)

Dear Mr. Perkins, Attached is the report associat ed with four (4) aqueous sa mples submitted for selenium speciation analysis on March 8, 2011. The sa mples were received on March 9, 2011 in a sealed cooler at -0.4 o 

## C. Selenium speciation anal ysis was performed via ion chromatography inductively coupled plasma dynamic reaction cell mass spectrometry (IC-ICP-DRC-MS). Any analytical issues asso ciated with the analysis are addressed in the following report. If you have any questions, please feel fr ee to contact me at your convenience.
Sincerely,

Russell Gerads Vice President Applied Speciation and Consulting, LLC

## Applied Speciation and Consulting, LLC Report prepared for: Jay Perkins Duke Energy Analytical Laboratory Mail Code MGO3A2 (Building 7405) 13339 Hagers Ferry Rd. Huntersville, NC 28078
Project: Allen – FGD Alternative Fuels Test Burn #3 - Daily) (LIMS # J11030112)

March 21, 2011

1. Sample Reception Four (4) aqueous samples in 125mL HDPE bottles (provided by Applied Speciation and Consulting) were submitted for selenium speciation analysis on March 8, 2011. The samples were received on March 9, 2011 in a sealed container at -0.4 o 

## C. The samples were received in a lamina r flow clean hood void of trace metals contamination and ultra-violet radiat ion. Upon reception, the samples were designated discrete sample identifiers. An aliquot of each sample was filtered (0.45μm) and these filtrates were stored in a secure, monitored cryofreezer (maintained at a temperature of -80 o 

## C) until selenium speciat ion analysis could be performed via ion chromatography inductive ly coupled plasma dynamic reaction cell mass spectrometry (IC-ICP-DRC-MS).

2. Sample Preparation All sample preparation is performed in laminar flow clean hoods known to be free from trace metals contamination. All a pplied water for dilutions and sample preservatives are monitored for contamina tion to account for any biases associated with the sample results. Selenium Speciation Analysis by IC-ICP-DRC-MS Prior to analysis , an aliquot of each sample was filtered with a syringe filt er (0.45μm) and inject ed directly into a sealed autosampler vial. No further sa mple preparation was performed as any chemical alteration of the samples may shift the equilibrium of the system resulting in changes in speciation ratios.

## 3. Sample Analysis All sample analysis is precluded by a minimum of a five-poi nt calibration curve spanning the entire concentrati on range of interest. Calibration curves are performed at the beginning of each analytical day. All calibration curves, associated with each species of interest, are sta ndardized by linear regression re sulting in a response factor. All sample results are instrument blank corrected to account for any operational biases associated with the analytical platform. Prior to sample analysis, all calibration curves are ve rified using second source standards which are identified as initial calibration verification standards (ICV). Ongoing instrument performance is iden tified by the analysis of continuing calibration verification standards (CCV) and continuing calibration blanks (CCB) at a minimal interval of every ten analytical runs. Selenium Speciation Anal ysis by IC-ICP-DRC-MS All samples for selenium speciation analysis were analyzed by ion chromatography inductively coupled plasma dynamic reaction cell mass spectrometry (IC-ICP-DRC-MS) on March 11, 2011. An aliquot of each sample is injected onto an anion exchange column and mobilized by a basic (pH > 7) gradient. The eluting selenium species are then introduced into a radio frequency (RF) plasma where energy-tr ansfer processes cause desolvation, atomization, and ionization. The ions are extracted from the plasma through a differentially-pumped vacuum interface and travel through a pressurized chamber (DRC) containing a specific reactive gas whic h preferentially reacts with interfering ions of the same target mass to charge ratios (m/z). A solid-state detector detects ions transmitted through the mass analyzer and the resulting current is processed by a data handling system. Retention times for each eluting species are compared to known standards for species identification.
4. Analytical Issues The overall analyses went very well and no analytical issues were encountered. All quality control parameters associated with these samples were within acceptance limits.
The estimated method detection limits (eMDLs) for selen ite, selenate, and selenocyanate are generated from replicate analyses of the lowest standard in the calibration curve. Not all selenium speci es are present in preparation blanks; therefore, eMDL calculations based on preparat ion blanks are artificially biased low.

## The eMDL for methylseleninic acid and selenomethionine is calculated from the average eMDL of selenite, selenate, and selenocyanate. The calibration does not contain methylseleninic acid or selenomethionine due to impurities in these standards which would bias the results for other selenium species. The selenocyanate recoveries for the ma trix spike and matrix spike duplicates performed on the sample identified as Batch QC were below the established control limit of 75% (0.0%). The selenite recoveries for the matrix spike and matrix spike duplicate were 188.3% and 188.2%, respecti vely. The low selenocyanate and the elevated selenite recoveries are attributed to the sample matrix inducing oxidation of selenocyanate to selenite. The ambient sample concentrations support the oxidative nature of the samples since only oxidized se lenium species were present. The quality control discrepancies were a function of the sample matrix; therefore, no corrective action was required. If you have any questions or concerns regarding this report, please feel free to contact me. Sincerely,

Russell Gerads Vice President Applied Speciation and Consulting, LLCSample ResultsSample IDSe(IV) Se(VI) SeCN MeSe(IV) SeMeUnknown SeSpecies (n)FGD Purge EffND (<2.4) 1250 ND (<3.0) ND (<3.0) ND (<3.0) 0 (0)BioReactor 1 Inf6.62871 ND (<0.76) ND (<0.75) ND (<0.75) 0 (0)BioReactor 2 Inf1.15 ND (<0.90) ND (<0.76) ND (<0.75) ND (<0.75) 0 (0)BioReactor 2 Eff1.17 ND (<0.90) ND (<0.76) ND (<0.75) ND (<0.75) 0 (0)All results reflect the applied dilution and are reported in μg/LND = Not detected at the applied dilutionSeCN = SelenocyanateMeSe(IV) = Methylseleninic acidSeMe = SelenomethionineUnknown Se Species = Total concentration of all unknown Se species observed by IC-ICP-MSn = number of unknown Se species observedReport Generated by: Russell GeradsApplied Speciation and Consulting, LLCSelenium Speciation Results for Duke EnergyProject Name: Allen - FGD Alternative Fuels Test Burn #3 - DailyContact: Jay PerkinsDate: March 21, 2011LIMS #J11030112Quality Control Summary - Preparation Blank SummaryAnalyte (μg/L) PBW1 PBW2 PBW3 PBW4 Mean StdDev eMDL* eMDL 50x eMDL 200xSe(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.012 0.60 2.4Se(VI) 0.000 0.000 0.000 0.000 0.000 0.000 0.018 0.90 3.6SeCN 0.000 0.000 0.000 0.000 0.000 0.000 0.015 0.76 3.0MeSe(IV) 0.000 0.000 0.000 0.000 0.000 0.000 0.015 0.75 3.0SeMe 0.000 0.000 0.000 0.000 0.000 0.000 0.015 0.75 3.0eMDL = Estimated Method Detection Limit*Please see narrative regarding eMDL calculationsQuality Control Summary - Certified Reference MaterialsAnalyte (μg/L) CRM True Value Result RecoverySe(IV) ICV 9.57 9.59 100.2Se(VI) ICV 9.48 9.05 95.4SeCN ICV 8.92 8.87 99.5MeSe(IV) ICV 6.47 5.73 88.6SeMe ICV 9.32 8.42 90.4Selenium Speciation Results for Duke EnergyProject Name: Allen - FGD Alternative Fuels Test Burn #3 - DailyContact: Jay PerkinsLIMS #J11030112Date: March 21, 2011Report Generated by: Russell GeradsApplied Speciation and Consulting, LLCQuality Control Summary - Matrix DuplicatesAnalyte (μg/L) Sample ID Rep 1 Rep 2 Mean RPDSe(IV) Batch QC 1.30 1.10 1.20 16.4Se(VI) Batch QC ND (<0.90) ND (<0.90) NC NCSeCN Batch QC ND (<0.76) ND (<0.76) NC NCMeSe(IV) Batch QC ND (<0.75) ND (<0.75) NC NCSeMe Batch QC ND (<0.75) ND (<0.75) NC NCND = Not detected at the applied dilutionNC = Value was not calculated due to one or more concentrations below the eMDLQuality Control Summary - Matrix Spike/ Matrix Spike DuplicateAnalyte (μg/L)Sample ID Spike Conc MS Result Recovery Spike Conc MSD Result Recovery RPDSe(IV)Batch QC 278.0 524.5 188.3 278.0 524.5 188.2 0.0Se(VI)Batch QC 252.3 256.1 101.5 252.3 256.6 101.7 0.2SeCNBatch QC 228.8 0.0 0.0* 228.8 0.0 0.0* 0.0*The low recovery is attributed to matrix induced species conversionSelenium Speciation Results for Duke EnergyProject Name: Allen - FGD Alternative Fuels Test Burn #3 - DailyContact: Jay PerkinsLIMS #J11030112Date: March 21, 2011Report Generated by: Russell GeradsApplied Speciation and Consulting, LLC3958 6 th Ave NW • Seattle, WA 98107 • T: 206

- 632

- 6206 • F: 206

- 632

- 6017 • www.brooksrand.com • brl@brooksrand.com 

### March 20, 2011
Duke Energy ATTN : Jay Perkins Scientific Support

- Laboratory 13339 Hagers Ferry Road Huntersville NC 28078 jcperkins@duke

- energy.com labcustomer@duke

- energy.com

RE: Project DUK

- HV100 1 Client P roject : J1 1 030112
Dear Mr. Perkins, O n March 9 , 2011 , Brooks Rand Labs ( BRL ) received three ( 3 ) flue gas desulfurization ( FGD ) waste water samples and three (3) field blanks (one from each related FGD sample site)

. All samples were logged

- in for total mercury (Hg) analysis and were received, prepared, analyzed, and stored according to BRL SOPs and EPA methodology. The results were blank

- corrected as described in the calculations section of the applicable SOP(s) and may be evaluated using adjusted reporting limits to account for sample aliquot size. Please refer to the Sample Results page for sample

- specific detection limits and other details

. Aside from concentration qualifiers, all data was reported without qualification and a ll quality assurance criteria were satisfied. The analysis of the low calibration standard (1100161

- CAL1) produced an abnormal peak sh ape. The low calibration standard was re - analyzed as 1100161

- CAL6 and the re

- analysis was reported . No additional corrective action was required. BRL, an accredited laboratory, certifies the reported results of all analyses for which BRL is NELAP accredited meet all NELAP requirements. For more details , see the Report Information page of the report. Please feel free to contact us if you have any questions regarding this report.
Sincerely,

Tiffany Stilwater Lydia Greaves Project Manager Project Coordinator tiffany @brooksrand.com l y dia @brooksrand.comProject ID: DUK-HV1101

PM: Tiffany Stilwater Client PM: Jay Perkins Client PO: 141391



### Definition of Data Qualifiers

(Effective 9/23/09) 

### Laboratory Accreditation BRL is accredited by the National Environmental Laboratory Accreditation Program (NELAP) through the State of Florida Department of Health, Bureau of Laboratories (E87982) and is certified to perform many environmental analyses. BRL is also certified by many other states to perform environmental analyses. For a current list of our accreditations /certifications, please visit our website at <http://www.brooksrand.com/default.asp?contentID=586>. Results reported relate only to the samples listed in the report. 

# Report Information

BLK BRL BS CAL CCV
CRM D DUP ICV MSD ND NR PS REC RPD RSD SCV SOP method blank Brooks Rand Labs laboratory fortified blank calibration standard continuing calibration verification
certified reference material dissolved fraction duplicate initial calibration verification matrix spike duplicate non-detect non-reportable post preparation spike percent recovery relative percent difference relative standard deviation secondary calibration verification standard operating procedure MDL MRL MS

method detection limit method reporting limit matrix spike

SRM T COC

standard reference material total recoverable fraction chain of custody record 

### Common Abbreviations

These qualifiers are based on those previously utilized by Brooks Rand, Ltd., those found in the EPA SOW ILM03.0, Exhibit B, Section III, pg. B-18, and the USEPA Laboratory Data Validation Functional Guidelines for Evaluating Inorganic Analyses; USEPA; July 2002. These supersede all previous qualifiers ever employed by BRL. Detected by the instrument, the result is > the MDL but ≤ the MRL. Result is reported and considered an estimate. B E An estimated value due to the presence of interferences. A full explanation is presented in the narrative. H Holding time and/or preservation requirements not met. Result is estimated. J Estimated value. A full explanation is presented in the narrative. J-M Duplicate precision (RPD) for associated QC sample was not within acceptance criteria. Result is estimated. J-N Spike recovery for associated QC sample was not within acceptance criteria. Result is estimated. M Duplicate precision (RPD) was not within acceptance criteria. Result is estimated. N Spike recovery was not within acceptance criteria. Result is estimated. R Rejected, unusable value. A full explanation is presented in the narrative. U Result is ≤ the MDL or client requested reporting limit (CRRL). Result reported as the MDL or CRRL. X Result is not BLK-corrected and is within 10x the absolute value of the highest detectable BLK in the batch. Result is estimated. 

### Field Quality Control Samples Please be notified that certain EPA methods require the collection of field quality control samples of an appropriate type and frequency; failure to do so is considered a deviation from some methods and for compliance purposes should only be done with the approval of regulatory authorities. Please see the specific EPA methods for details regarding required field quality control samples.

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.comProject ID: DUK-HV1101

PM: Tiffany Stilwater Client PM: Jay Perkins Client PO: 141391



# Sample Information

Report Matrix Type Received Sampled Sample Lab ID 1111021-01 BioReactor 1 Inf 03/03/2011 03/09/2011 Sample FGD Wastewater 1111021-02 BioReactor 1 Inf Hg Blk 03/03/2011 03/09/2011 Field Blank DIW 1111021-03 BioReactor 2 Inf 03/03/2011 03/09/2011 Sample FGD Wastewater 1111021-04 BioReactor 2 Inf Hg Blk 03/03/2011 03/09/2011 Field Blank DIW 1111021-05 BioReactor 2 Eff 03/03/2011 03/09/2011 Sample FGD Wastewater 1111021-06 BioReactor 2 Eff Hg Blk 03/03/2011 03/09/2011 Field Blank DIW 

# Batch Summary

Analyte Prepared Analyzed Sequence Batch Lab Matrix Method B110373 03/11/2011 03/14/2011 1100161 Water EPA 1631 Hg

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.comProject ID: DUK-HV1101

PM: Tiffany Stilwater Client PM: Jay Perkins Client PO: 141391



# Sample Results

Sample Sequence Result MDL MRL Unit Batch

Qualifier Analyte Fraction

Report Matrix BioReactor 1 Inf ng/L 317 T 1100161 B110373 FGD Wastewater 20.2 7.58 1111021-01 Hg
BioReactor 1 Inf Hg Blk ng/L 0.15 T U 1100161 B110373 DIW 0.40 0.15 1111021-02 Hg

BioReactor 2 Eff ng/L 11.8 T 1100161 B110373 FGD Wastewater 0.81 0.30 1111021-05 Hg
BioReactor 2 Eff Hg Blk ng/L 0.15 T U 1100161 B110373 DIW 0.40 0.15 1111021-06 Hg

BioReactor 2 Inf ng/L 30.0 T 1100161 B110373 FGD Wastewater 1.59 0.60 1111021-03 Hg
BioReactor 2 Inf Hg Blk ng/L 0.15 T U 1100161 B110373 DIW 0.40 0.15 1111021-04 Hg

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.comProject ID: DUK-HV1101

PM: Tiffany Stilwater Client PM: Jay Perkins Client PO: 141391



# Accuracy & Precision Summary

Analyte Result Units

Native Spike REC & Limits RPD & Limits Batch: B110373

Method: EPA 1631 Lab Matrix: Water

Sample Certified Reference Material (1111049, NIST 1641d 1000x dilution) B110373-SRM1 15.68 98% ng/L 85-115 Hg 15.35 Reference Matrix Spike (1111021-03) B110373-MS1 141.2 102% ng/L 71-125 Hg 174.0

30.02 Matrix Spike Matrix Spike Duplicate (1111021-03) B110373-MSD1 136.3 109% ng/L 71-125 242% Hg 178.2

30.02 Matrix Spike Dup



# Method Blanks & Reporting Limits

Batch: B110373

Method: EPA 1631 Matrix: Water
Analyte: Hg Result Units Sample B110373-BLK1 0.05 ng/L B110373-BLK2 0.05 ng/L B110373-BLK3 0.04 ng/L B110373-BLK4 0.16 ng/L MDL: 0.15

Average: 0.08 Standard Deviation: 0.06 Limit: 0.10 Limit: 0.50 MRL: 0.40

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.comProject ID: DUK-HV1101

PM: Tiffany Stilwater Client PM: Jay Perkins Client PO: 141391



# Instrument Calibration

Method: EPA 1631 Sequence: 1100161 Instrument: THG-10 Date: 03/14/2011 Total Mercury and Mercury Speciation by CVAFS

Analyte: Hg REC & Limits Result True Value Lab ID Units 1100161-IBL1 pg of Hg 4.06 1100161-IBL2 pg of Hg 3.56 1100161-IBL3 pg of Hg 5.41 1100161-IBL4 pg of Hg 4.42 100.0 1100161-CAL2 100% pg of Hg 99.70 500.0 1100161-CAL3 100% pg of Hg 500.9 2500 1100161-CAL4 99% pg of Hg 2480 10000 1100161-CAL5 97% pg of Hg 9684 1568 1100161-ICV1 98% pg of Hg 85-115 1535 1100161-CCB1 pg of Hg 12.4 25.00 1100161-CAL6 104% pg of Hg 26.09 500.0 1100161-CCV2 94% pg of Hg 77-123 469.2 500.0 1100161-CCV3 94% pg of Hg 77-123 471.4 500.0 1100161-CCV4 102% pg of Hg 77-123 508.1

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.comProject ID: DUK-HV1101

PM: Tiffany Stilwater Client PM: Jay Perkins Client PO: 141391



# Sample Containers

Lab ID: 1111021-01 Report Matrix: FGD Wastewater Sample Type: Sample Received: 03/09/2011 Sample: BioReactor 1 Inf Collected: 03/03/2011
Ship. Cont. pH P-Lot Preservation Lot Size Container Des A 71281400 20 Cardboard Box None N/A 250-mL Bottle FLPE Hg-T

Lab ID: 1111021-02 Report Matrix: DIW Sample Type: Field Blank Received: 03/09/2011 Sample: BioReactor 1 Inf Hg Blk Collected: 03/03/2011
Ship. Cont. pH P-Lot Preservation Lot Size Container Des A 71281400 20 Cardboard Box None N/A 250-mL Bottle FLPE Hg-T

Lab ID: 1111021-03 Report Matrix: FGD Wastewater Sample Type: Sample Received: 03/09/2011 Sample: BioReactor 2 Inf Collected: 03/03/2011
Ship. Cont. pH P-Lot Preservation Lot Size Container Des A 71280600 20 Cardboard Box None N/A 500 mL Bottle FLPE Hg-T

Lab ID: 1111021-04 Report Matrix: DIW Sample Type: Field Blank Received: 03/09/2011 Sample: BioReactor 2 Inf Hg Blk Collected: 03/03/2011
Ship. Cont. pH P-Lot Preservation Lot Size Container Des A 71280600 20 Cardboard Box None N/A 500 mL Bottle FLPE Hg-T

Lab ID: 1111021-05 Report Matrix: FGD Wastewater Sample Type: Sample Received: 03/09/2011 Sample: BioReactor 2 Eff Collected: 03/03/2011
Ship. Cont. pH P-Lot Preservation Lot Size Container Des A 71138980 50 Cardboard Box None N/A 250 mL. Bottle FLPE Hg-T

Lab ID: 1111021-06 Report Matrix: DIW Sample Type: Field Blank Received: 03/09/2011 Sample: BioReactor 2 Eff Hg Blk Collected: 03/03/2011
Ship. Cont. pH P-Lot Preservation Lot Size Container Des A 71138980 50 Cardboard Box None N/A 250-mL Bottle FLPE Hg-T

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.comProject ID: DUK-HV1101

PM: Tiffany Stilwater Client PM: Jay Perkins Client PO: 141391



# Shipping Containers

Cardboard Box
Tracking No: 4726 7965 8274 via FedEx Temperature: ambient Coolant Type: None Description: Cardboard Box Damaged in transit? No Returned to client? No Custody seals present? No Custody seals intact? No COC present? Yes Received: March 9, 2011 9:20

3958 6th Avenue NW Seattle WA 98107 · P(206) 632-6206 · F(206) 632-6017 · brl@brooksrand.com · www.brooksrand.com