CASE STUDY 

Fire and Community Evacuation in 

Apex, North Carolina 

2007-01-I-NC 

April 16, 2008 

Photograph courtesy of Wake County Fire/Rescue Services 

Environmental Quality Company 

Apex, North Carolina 

October 5, 2006

Key Issues: 

• Facility Fire Detection 

• Facility Fire Protection 

• Emergency Planning 

Introduction 

This case study examines a fire 

at a hazardous waste facility 

located in Apex, North Carolina. 

City officials ordered thousands 

of local residents to evacuate for 

two days. About 30 people 

sought medical attention. The 

CSB makes recommendations to 

the US Environmental Protection 

Agency and Environmental 

Technology Council to address 

emergency planning and fire 

protection requirements for 

hazardous waste facilities. 

INSIDE . . . 

Incident Description 

Background 

Analysis 

Regulatory Analysis 

Conclusions 

Recommendations 

References
EQ North Carolina Case Study April 2008 

2

1.0 Incident Description 

This case study examines a fire at the 

Environmental Quality Company (EQ) 

hazardous waste facility in Apex, North 

Carolina, and the subsequent community 

evacuation. 

At 9:38 pm on October 5, 2006, a citizen 

driving past the EQ facility called 911 to 

report a haze with a “strong chlorine smell.” 

The Apex 911 center dispatched emergency 

personnel to investigate. 

Responding Apex Fire Department 

personnel discovered a chemical cloud 

coming from one of several businesses on 

Investment Boulevard. The Apex Fire 

Chief, acting as the Incident Commander 

(IC), sent two firefighter reconnaissance 

teams in personal protective equipment to 

investigate the source of the cloud. 

Firefighters located a small “sofa-size” fire 

in one of the hazardous waste bays at the EQ 

facility. Within minutes, the fire spread to 

the flammable liquid storage area, causing 

55-gallon drums of flammable hazardous 

waste to explode and sending fireballs 

hundreds of feet into the air. The hazardous 

waste building ultimately collapsed (cover 

photograph). 

During the incident, about 30 people 

(including 13 first responders) sought 

medical attention at local hospitals for 

respiratory distress and nausea. Some were 

treated; none was admitted. 

1.1 Emergency Response 

Because of the unknown nature of the 

burning chemicals and the exploding drums, 

the IC chose to take only defensive actions 

to 

• minimize the risk to emergency 

personnel and community residents, and 

• allow the fire to burn and consume the 

chemicals within the facility. 

The defensive actions included 

• ordering a precautionary evacuation of 

thousands of residents in the surrounding 

community,1

 

• controlling access on roads leading into 

the evacuation area, 

• stopping rail traffic through the 

community, and 

• closing the air space over the facility. 

EQ contracted an industrial firefighting and 

environmental cleanup company with 

specialized equipment to extinguish the fire 

and clean up the site. The contractor 

• built sand berms to minimize water 

runoff that could possibly contaminate 

an adjacent stream, 

• removed the roof and structural steel to 

access the burning waste, 

• extinguished the fire with foam, and 

• removed all debris and hazardous waste 

from the site. 

1.2 Community Evacuation 

The evacuation area included about 3,300 

residences, the town hall, a fire station, and 

the town 911 center.2

 Officials established 

 

1

 A call down, or reverse 911 system, called homes in 

the evacuation area and disseminated the order with a 

recorded message. Several television stations also 

ran a ticker notification message. 

 

2

 Apex 911 personnel transferred incoming 911 calls 

to the Raleigh, NC, 911 center. 
EQ North Carolina Case Study April 2008 

3

an Emergency Operations Center (EOC) 

outside of the evacuation area to provide a 

safe gathering place for emergency 

responders, state and federal officials, and 

media representatives. 

Evacuees from the community sheltered at 

designated elementary schools, in hotels, or 

with relatives outside the evacuation area. 

The Red Cross, other community 

organizations, and businesses assisted 

residents by providing bedding, food, and 

communication services. 

The IC continued the evacuation order for 

two days because of potential re-ignition and 

persistent smoke from the smoldering 

rubble. 

1.3 Environmental Impact 

The North Carolina Department of 

Environmental and Natural Resources 

(NCDENR) Divisions of Air Quality, Water 

Quality, Environmental Heath, and Waste 

Management and the US Environmental 

Protection Agency (EPA) responded to the 

incident. In the early morning of October 6, 

2006, (about five hours after the fire was 

first reported) the NCDENR and the EPA 

began air monitoring within the evacuation 

area. In addition to ground level 

monitoring, the EPA conducted 10 fly-overs 

with its Airborne Spectral Photographic 

Environmental Collection Technology 

(ASPECT) aircraft. 

EQ also contracted with a company 

specializing in environmental monitoring, 

testing and assessment to conduct ground 

level atmospheric monitoring beginning 

October 6, 2006. 

In the weeks following the incident, the 

NCDENR looked for residual contamination 

by conducting soil, indoor environmental, 

and exterior swipe sampling for a range 

organic and inorganic materials.3 On 

November 17, 2006, the NCDENR reported 

that “environmental tests show no offsite 

contamination from EQ fire.” 

 

3

 NCDENR sampling reports are available at 

http://www.enr.state.nc.us/html/eq_offsite.html. 
EQ North Carolina Case Study April 2008 

4

2.0 Background 

2.1 The Environmental Quality 

Company 

Headquartered in Wayne, Michigan, EQ 

operates hazardous and non-hazardous waste 

treatment, storage, and disposal facilities at 

20 locations in the United States. 

The EQ facility in Apex, North Carolina,4

 

(known as EQ North Carolina, or EQNC) 

provided hazardous and non-hazardous 

waste bulking,5 solidification, storage, and 

transfer. Businesses served included 

research and development facilities, 

educational institutions, manufacturing 

companies, government entities, retail 

stores, and medical facilities. 

Enviro-Chem Environmental Services, Inc. 

constructed and operated the Apex 

hazardous waste facility beginning in 1992. 

EQ acquired the facility in December 2002 

and began operating under the Enviro-Chem 

Environmental Services, Inc. permit in 

January 2003. In May 2003, the NCDENR 

issued EQ a permit to operate the facility. 

EQNC normally operated Monday through 

Friday from 7:00 am to 4:00 pm with a staff 

of 15 EQNC and 12 contract employees. 

The facility included two buildings: 

• a two-story building with offices, 

employee change room, chemical 

laboratory, and non-hazardous waste 

processing area; and 

• a one-story building for hazardous waste 

handling. 

 

4

 Following the October 5, 2006, fire, EQ 

discontinued operations at the Apex, NC, facility. 

5

 Bulking refers to combining small containers of 

similar materials into a larger container. 

The hazardous materials building had a 

metal pitched roof, metal walls enclosing 

opposite ends, and open sides. Inside the 

building were six bays for handling and 

storing the hazardous waste. An elevated 

shipping and receiving dock in the center of 

the building and six-inch-high by three-footwide curbs separated the bays. EQNC 

designated each bay for a specific waste 

type (Figure 1) to separate incompatible 

materials.6

 

Figure 1. EQNC hazardous materials 

building 

Portable fire extinguishers located on each 

side of the central dock provided fire 

protection for the building. A chain-link 

fence with a padlocked gate secured the 

facility. 

2.2 Environmental Technology 

Council 

 

6

 When mixed, incompatible materials may react with 

each other, producing heat, fire, and/or toxic vapors. 
EQ North Carolina Case Study April 2008 

5

The Environmental Technology Council 

(ETC) is a trade association of commercial 

environmental firms that recycle, treat, and 

dispose of industrial and hazardous waste, 

and includes firms specializing in 

contaminated site cleanup. ETC member 

companies handle about 80 percent of the 

hazardous waste market in the United States. 

EQ is a member of ETC. 

2.3 State of North Carolina 

The North Carolina Department of Environment 

and Natural Resources (NCDENR), Division of 

Waste Management regulates hazardous waste 

facilities. 

Following the October 5, 2006 incident in Apex, 

the Governor of North Carolina formed a 

Hazardous Materials Task Force to examine the 

regulations for hazardous waste storage 

facilities. This task force made 16 regulatory 

recommendations and six funding 

recommendations, which became the basis of 

changes to the North Carolina hazardous waste 

statutes enacted by the NC legislature in June 

2007.7

 

 

7

 The Governor’s Task Force report and legislative 

changes are available at respectively: 

http://www.enr.state.nc.us/docs/HazardousWasteTas

kforceReport.pdf

http://www.ncga.state.nc.us/Sessions/2007/Bills/Hou

se/HTML/H36v4.html . 
EQ North Carolina Case Study April 2008 

6

3.0 Analysis 

3.1 Hazardous Waste Facility 

Fires and Releases 

3.1.1 EQNC Incidents 

NCDENR Incident Reports and employee 

interviews document prior incidents at 

EQNC, including leaking and broken 

containers as well as smoking and 

spontaneously combusting materials.8 

Employees discovered all of these incidents 

during normal working hours and they were 

corrected without outside assistance. 

3.1.2 EQ Romulus Michigan Fire 

On August 9, 2005, an EQ hazardous waste 

facility in Romulus, Michigan, caught fire 

and burned. Although the causes were 

different from the EQNC fire, the 

firefighters in Romulus also chose to take 

only defensive actions due to the intensity of 

the fire and their lack of knowledge about 

the facility’s contents. Romulus officials 

also ordered a precautionary evacuation of 

residents within one mile of the facility. One 

EQ employee was injured. 

3.1.3 Industry Incidents 

In addition to the EQ incidents, the CSB 

found 21 other fire and chemical release 

incidents9

 at hazardous waste facilities in the 

United States in the last five years. Fourteen 

of the incidents involved fires and/or 

explosions and seven were release-only 

incidents. These incidents resulted in two 

fatalities, 16 injuries, and eight community 

evacuations, shelter-in-place events, or 

transportation disruptions. 

 

8

 These incidents included a fire on July 3, 2006, in a 

cubic-yard box packed with laboratory waste, debris, 

and flammable solids. 

9

 None of these incidents occured in North Carolina 

3.2 Fire Detection 

Even though the facility stored hundreds of 

55-gallon drums of flammable and 

combustible materials, the EQNC hazardous 

waste building was not required to be 

equipped with fire or smoke detection 

sensors nor monitored after hours (nights or 

weekends). 

Continuous monitoring by personnel or with 

remotely monitored sensors can alert 

company personnel and first responders at 

the inception of a fire. This may provide 

first responders additional time to initiate 

emergency actions before the situation 

grows out of control. 

3.3 Fire Control Equipment 

Portable fire extinguishers were the only fire 

control equipment in the EQNC hazardous 

waste building. The facility included 

segregated areas (storage bays) for different 

waste types separated by six-inch-high 

curbs. The curbs could contain spills within 

the bays, but would not prevent a fire from 

spreading from one bay to another. 

The initial “sofa-size” fire observed by 

firefighters was in the oxidizer bay where a 

fiberboard container of unspent aircraft 

oxygen generators10 and containers of solid 

chlorine-based pool chemicals were 

awaiting final shipment.11 Figure 2 shows 

an oxygen generator found in the debris with 

its activation pin in place, indicating that it 

was unspent when the fire started. Because 

oxygen generators were located at or near 

the origin of the fire and, when exposed to 

 

10 The CSB issued a Safety Advisory in June 2007 

addressing the hazards associated with transporting 

and storing expired, unspent aircraft chemical oxygen 

generators. 

11 The cause of the initial fire was never determined. 
EQ North Carolina Case Study April 2008 

7

fire, produce oxygen that significantly 

increases the intensity of a fire, the CSB 

concluded that the unspent oxygen 

generators most likely contributed to the 

rapid spread of the fire to the adjacent bay 

where flammable hazardous wastes were 

stored. 

Figure 2. Oxygen generator with activation 

pin circled 

While not required, had EQNC used fire 

barriers (walls) to separate the segregated 

waste bays, the fire would likely have been 

contained within the oxidizer bay, 

significantly mitigating the incident’s 

consequences. 

The National Fire Protection Association 

(NFPA) publishes fire protection standards 

for many industrial facility types12 (e.g. 

NFPA 820, “Standard for Fire Protection in 

Wastewater Treatment and Collection 

Facilities”). These standards address fire 

protection requirements specific to the 

facility type. However, no standard 

specifically addresses fire protection for 

 

12 Also known as occupancy standards. 

hazardous waste treatment, storage, and 

disposal facilities. 

A review by CSB of fire protection practices 

in use at 12 other hazardous waste 

facilities13 showed wide variation. Some 

facilities use active fire suppression systems 

to control or extinguish fires, some use fire 

barriers, and others, like EQNC, rely only on 

portable fire extinguishers. 

3.4 Emergency Planning 

Apex fire personnel identified the EQNC 

facility as the source of the chemical cloud 

and fire; however, EQNC had not provided 

any detailed written information on the 

types, quantities, and location of hazardous 

materials in the facility to fire personnel or 

the Local Emergency Planning Committee 

(LEPC). Additionally, since the EQNC 

facility was unoccupied at the time of the 

incident, no emergency coordinator was onsite to initiate the facility contingency plan14

or assess the extent of the release or 

emergency. 

Other companies in the Town of Apex 

provided information to the fire department 

on the types, quantities, and location of 

hazardous materials the companies handled. 

The fire department used this information 

for emergency planning and conducted joint 

emergency drills with several of these 

companies. 

When companies provide written 

information on the approximate quantity, 

hazards, and location of materials within 

their facilities to fire departments, police 

departments, hospitals, and LEPCs, 

responders can preplan for emergencies. 

 

13 This number includes facilities in North Carolina 

and several other states. 

14 An emergency plan required for permitted 

hazardous waste facilities (section 4.1.3). 
EQ North Carolina Case Study April 2008 

8

4.0 Regulatory Analysis 

4.1 The Resource 

Conservation and 

Recovery Act 

The Resource Conservation and Recovery 

Act (RCRA) authorizes the EPA to regulate 

the generation, treatment, storage, and 

disposal of hazardous waste. EPA 

regulations implementing RCRA provide a 

“cradle-to-grave” management system for 

hazardous waste. The intent of this system 

is for generators, transporters, and facilities 

that treat, store, and dispose of hazardous 

waste to take responsibility for hazardous 

waste throughout its life cycle through final 

disposal to protect the public and the 

environment. 

In most cases, the EPA authorizes states to 

implement the RCRA hazardous waste 

management program. State regulations 

must be at least as stringent as, and may be 

more stringent than, the federal regulations. 

4.1.1 Implementing Regulations 

EPA regulations implementing RCRA 

require businesses that generate hazardous 

waste to send the waste to a treatment, 

storage, or disposal facility (TSDF) 

permitted by the EPA or state environmental 

regulatory authority (NCDENR, in this case) 

to store, treat, or otherwise dispose of the 

waste. The EPA regulations establish 

minimum requirements for TSDF permits.15 

The permit is a facility-specific document 

that grants the facility the authority to store, 

treat, or dispose of hazardous waste as 

described in its permit application for a 

period of ten years. Permit requirements 

include, but are not limited to, 

 

15 40 CFR 264, “Standards for Owners and Operators 

of Hazardous Waste Treatment, Storage, and 

Disposal Facilities.” 

• waste analysis plan; 

• site security; 

• inspection procedures; 

• ignitable, reactive, and incompatible 

waste control plan; 

• emergency preparedness and prevention, 

including fire protection and 

communication; 

• contingency plan and emergency 

procedures; 

• arrangements with local authorities that 

include sharing copies of the 

contingency plan; 

• operating records; 

• management of containers, tanks, 

surface impoundments, and waste piles; 

and 

• providing financial assurance for 

closure/post-closure and liability. 

The regulatory authority routinely inspects 

permitted TSDFs.16 Inspections include 

review documentation and operations to 

verify TSDF compliance with permit 

requirement. 

4.1.2 Fire Protection 

Requirements 

EPA regulations17 state: 

 All facilities must be equipped with 

the following, unless [italics in 

original] it can be demonstrated to 

the [EPA] Regional Administrator 

that none of the hazards posed by 

waste handled at the facility could 

 

16 NCDENR inspected the EQNC facility several 

times each month. 

17 40 CFR 264.32 
EQ North Carolina Case Study April 2008 

9

require a particular kind of 

equipment specified below: ... 

(c) Portable fire extinguishers, fire 

control equipment (including special 

extinguishing equipment, such as 

that using foam, inert gas, or dry 

chemicals), spill control equipment, 

and decontamination equipment; and 

(d) Water at adequate volume and 

pressure to supply water hose 

streams, or foam producing 

equipment, or automatic sprinklers, 

or water spray systems. 

These are the only fire protection measures 

that EPA regulations require for TSDFs. 

Additionally, EPA regulations do not require 

a fire protection professional or local fire 

officials to review the fire protection 

measures. 

Although required by EPA and NCDENR 

regulations the EQNC permit application did 

not describe “fire control equipment” nor 

include a justification for not installing it in 

accordance with 40 CFR 264.32 paragraph 

(c). Despite hundreds of gallons of 

flammable liquids and strong oxidizers 

routinely handled onsite, the EQ facility 

operated with only portable fire 

extinguishers, which provided limited 

protection for the facility and community. 

4.1.3 Emergency Planning 

Requirements 

EPA regulations require TSDFs to have a 

contingency plan outlining actions facility 

personnel will take in case of emergency, 

the arrangements the facility has with local 

authorities, and the location of emergency 

equipment within the facility. TSDFs must 

share the contingency plan with local 

authorities, including fire and police 

departments.18

In addition to the contingency plan, EPA 

regulations (40 CFR 264.37) require 

facilities to make 

“[a]rrangements to familiarize police, fire 

departments, and emergency response teams 

with the layout of the facility, properties of 

hazardous waste handled at the facility and 

associated hazards, places where facility 

personnel would normally be working, 

entrances to and roads inside the facility, 

and possible evacuation routes.” 

Although this requirement mandates that the 

facility operator familiarize local authorities 

with the facility, its layout, and its hazards, 

the requirements do not explicitly state what 

information must be shared, if the 

information must be written, or if updates 

are necessary. 

EQ met these requirements simply by 

having the Apex Fire Chief tour the facility 

once. 

4.2 The Emergency Planning 

and Community Right-toKnow Act 

The Emergency Planning and Community 

Right-to-Know Act (EPCRA) requires 

companies to notify local authorities 

(including fire departments and LEPCs) 

regarding certain chemicals that are stored 

and used onsite. EPA regulations 

implementing EPCRA improve community 

preparedness for chemical emergencies at 

local facilities by 

1. informing the public, 

2. facilitating response, and 

 

18 EQNC could not provide any documented evidence 

that this requirement was met. 
EQ North Carolina Case Study April 2008 

10

3. ensuring that emergency responders are 

aware of onsite hazards. 

The EPA reporting requirements for 

hazardous chemicals greater than specified 

quantities under the Community Right-ToKnow program include 

1. supplying Material Safety Data Sheets 

(MSDS) or a list of all hazardous 

chemicals present at the facility, and 

2. submitting an annual inventory report to 

local authorities and the fire department. 

The Community Right-to-Know reporting 

requirements apply only to facilities 

required to keep MSDS on their hazardous 

chemicals in accordance with the 

“Occupational Safety and Health 

Administration (OSHA) Hazard 

Communication Standard” (29 CFR 

1910.1200). However, OSHA excludes 

hazardous wastes from the requirements of 

this standard, including MSDS 

requirements. Therefore, unlike most 

industrial facilities, a TSDF is not required 

to submit a list of waste chemicals onsite nor 

an annual inventory of hazardous materials 

to local authorities. 
EQ North Carolina Case Study April 2008 

11

5.0 Conclusions

5.1 Fire Prevention 

The EQNC hazardous waste building was 

not equipped with fire or smoke detection 

sensors, automated fire suppression 

equipment, or fire barriers, even though the 

facility stored hundreds of 55-gallon drums 

of flammable and combustible materials. 

EPA regulations implementing RCRA 

require that facilities be equipped with “fire 

control equipment;” however, no EPA 

guidance or industry standard is available to 

facility owners, permitting agencies, and 

local fire officials to establish appropriate 

fire prevention, detection, control, and 

suppression measures. 

5.2 Emergency Planning 

EQNC had limited contact with the Apex 

Fire Department prior to the October 5, 2006 

fire. EQNC had not provided the fire 

department or county emergency agency 

with written information on the types, 

quantities, and locations of the hazardous 

materials in the facility prior to the incident. 

Although EPA regulations implementing 

RCRA require companies to familiarize 

local authorities with the facility, its layout, 

and its hazards, the regulations do not 

explicitly state what information must be 

shared, whether the information should be 

written, or if updates are necessary.
EQ North Carolina Case Study April 2008 

12

6.0 Recommendations 

6.1 US Environmental 

Protection Agency 

2007-01-I-NC-R1 

Ensure that the emergency response 

planning required for permitted hazardous 

waste treatment, storage, and disposal 

facilities (40 CFR 264.37) includes 

providing written information to state and 

local emergency response officials on the 

type, approximate quantities, and locations 

of materials within the facility (similar to 

reporting requirements of the Emergency 

Planning and Community Right-to-Know 

Act). Additionally, ensure that permit 

holders periodically update this information 

throughout the ten-year permit period. 

6.2 Environmental Technology 

Council 

2007-01-I-NC-R2 

Petition the National Fire Protection 

Association, following the guidelines of 

their “Codes and Standards Development 

Process” (http://www.nfpa.org/index.asp), to 

develop a fire protection standard 

(occupancy standard) specific to hazardous 

waste treatment, storage, and disposal 

facilities. This standard should address fire 

prevention, detection, control, and 

suppression requirements. 

2007-01-I-NC-R3 

Develop standardized guidance for the 

handling and storage of hazardous waste to 

reduce the likelihood of releases and fires at 

hazardous waste treatment, storage, and 

disposal facilities. 
EQ North Carolina Case Study April 2008 

13

7.0 References 

29 CFR 1910.1200, “Hazard Communication Standard”; Occupational Health and Safety 

Administration, US Government Printing Office: Washington, DC, 2007

40 CFR 264, “Standards for Owners and Operators of Hazardous Waste Treatment, Storage, and 

Disposal Facilities”; Environmental Protection Agency, US Government Printing Office: 

Washington, DC, 2007 . 

40 CFR “Subchapter J--Superfund, Emergency Planning, and Community Right-To-Know 

Programs”; Environmental Protection Agency, US Government Printing Office: 

Washington, DC, 2007. 

U.S. Chemical Safety and Hazard Investigation Board (USCSB), 2007. Safety Advisory,

Dangers of Unspent Aircraft Oxygen Generators, Report No. 2007-I-NC-01-SA, June 2007. 
EQ North Carolina Case Study April 2008 

14

The U.S. Chemical Safety and Hazard Investigation Board (CSB) is an independent Federal agency 

whose mission is to ensure the safety of workers, the public, and the environment by investigating and 

preventing chemical incidents. The CSB is a scientific investigative organization; it is not an enforcement 

or regulatory body. Established by the Clean Air Act Amendments of 1990, the CSB is responsible for 

determining the root and contributing causes of accidents, issuing safety recommendations, studying 

chemical safety issues, and evaluating the effectiveness of other government agencies involved in 

chemical safety. 

No part of the conclusions, findings, or recommendations of the CSB relating to any chemical accident 

may be admitted as evidence or used in any action or suit for damages. See 42 U.S.C. § 7412(r)(6)(G). 

The CSB makes public its actions and decisions through investigation reports, summary reports, safety 

bulletins, safety recommendations, case studies, incident digests, special technical publications, and 

statistical reviews. More information about the CSB is available at www.csb.gov.

CSB publications can be downloaded at 

www.csb.gov or obtained by contacting:

U.S. Chemical Safety and Hazard 

Investigation Board 

Office of Congressional, Public, and Board Affairs 

2175 K Street NW, Suite 400 

Washington, DC 20037-1848 

(202) 261-7600

CSB Investigation Reports are formal, 

detailed reports on significant chemical 

accidents and include key findings, root causes, 

and safety recommendations. CSB Hazard 

Investigations are broader studies of significant 

chemical hazards. CSB Safety Bulletins are 

short, general-interest publications that provide 

new or noteworthy information on 

preventing chemical accidents. CSB Case 

Studies are short reports on specific accidents 

and include a discussion of relevant prevention 

practices. All reports may contain include 

safety recommendations when appropriate. 

CSB Investigation Digests are plain-language 

summaries of Investigation Reports.