Facility_Information

facility_id utility_codelegal_owner_nam legl_operator_name e legal_address_ty legal_address pe legal_city legal_state legal_zip

3992 11479 Madison Gas and Electric Company Madison Gas and Electric Company legal owner133 S. Blair Street, P.O. Box 1231 Madison WI 53701

Page 1
Facility_Information

plant_namephysical_address phyical_cityphysical_statephysical_zipmailing_address mailing_citymailing_statemailing_zip

Blount Street717 East Main Street Madison WI 53703 P.O. Box 1231 Madison WI 53701-1231

Page 2
Facility_Information

RFA_small_entity ff_fired_coalff_fired_oil ff_fired_ngasff_fired_petcoke ff_fired_other ff_permitted_coal ff_permitted_oil ff_permitted_ngas

No TRUE FALSE TRUE FALSE TRUE TRUE TRUE TRUE

Page 3
Facility_Information

ff_permitted_petcoke ff_permitted_other deviation_reporting continuous_emissions cem_providedfacility_note

FALSE TRUE Deviations from and violations of applicable requirements must be submitted in a monitoring report madNo EPA Clean Air Markets Division Part I.2. Boiler Information- Boiler Information Tab -- Boiler ID 

Page 4
Facility_Information

oiler Information Tab -- Boiler ID 7 --- Design heat input, MMBtu/hr: 332 mmBtu/hr is the value in the Title V permit; actual design h

Page 5
Facility_Information

 in the Title V permit; actual design heat input from specifications: 313 mmBtu/hr on natural gas, and 306 mmBtu/hr on coal --- Present 

Page 6
Facility_Information

6 mmBtu/hr on coal --- Present maximum heat input, mmBtu/hr: 309 mmBtu/hr on natural gas, 310 mmBtu/hr on coal  --- MWe g

Page 7
Facility_Information

0 mmBtu/hr on coal  --- MWe gross/net capacity, summer: 244,000 lb/hr steam flow. No gross or net MW numbers are available as ca

Page 8
Facility_Information

net MW numbers are available as capacity tests are done by turbine and Boiler 7 discharges to a common header. --- Design steam tem

Page 9
Facility_Information

on header. --- Design steam temperature (o F): 825 degrees F --- Operating steam temperature (o F): 825 degrees F --- Stea

Page 10
Facility_Information

re (o F): 825 degrees F --- Steam pressure and temperature values refer to boiler conditions. --- Design steam reheat temperatur

Page 11
Facility_Information

--- Design steam reheat temperature (o F): NA --- Operating steam reheat temperature (o F): NA --Boiler ID 8 --- Design 

Page 12
Facility_Information

 --Boiler ID 8 --- Design heat input, MMBtu/hr: 544 mmBtu/hr is the value in the Title V permit; actual design heat input from spe

Page 13
Facility_Information

mit; actual design heat input from specifications: 544 mmBtu/hr on natural gas

Page 14
facility_contacts

facility_id contact_id contact_titlecontact_namecontact_phone1 contact_phone2 contact_email contact_primary

3992 1 Environmental Specialist - Air Quality Brenda Kubasik 6082527281 bkubasik@mge.com TRUE

Page 15
facility_coal_utilized

facility_id coal_type percentage_mass percentage_btu synfuel_typecoal_note

3992 bituminous 100 100

Page 16
facility_oil_utilized

facility_id oil_type percentage_volume percentage_btu other_type

Page 17
facility_other_materials

facility_id other_material permitted_burn actually_burnother_quantity other_quantity other_note _units rcra_utilize rcra_explain

3992 Biomass/switch grass TRUE FALSE 0 tons/year No

3992 Biomass/wood fuel TRUE FALSE 0 tons/year No

3992 Boiler cleaning waste liquids TRUE FALSE 0 tons/year No

3992 Paper derived fuel TRUE TRUE 1517 tons/year The annual average of the last 3 y No ears of usage.

3992 Waste oil contaminated absorbents TRUE FALSE 0 tons/year No

Page 18
facility_other_materials

rcra_explain

Page 19
boiler_information

facility_id boiler_id boiler_type boiler_otherbottom_design design_fuelheat_input max_heat_input MWe_capacity

3992 7 Other (specify Cell burner ) Dry Bottomcoal 332 310 1

3992 8 Wall firing - front firing Dry Bottomcoal 544 575 53.4

3992 9 Wall firing - front firing Dry Bottomcoal 544 575 53.2

Page 20
boiler_information

MWe_net_capacity design_gross_efficiency operating_gross_efficiency design_pressure operating_pressure design_tempoperating_temp design_reheat_multiple design_reheat_temp1

1 85.7 72.52 1000 825 1 1 FALSE 1

50.9 87.3 85.66 1525 1250 1 1 FALSE 1

50.1 87.3 85.16 1525 1250 1 1 FALSE 1

Page 21
boiler_information

design_reheat_temp2 operating_reheat_multiple operating_reheat_temp1 operating_reheat_temp2 hours_operatedvg_capacityapplicable_NSPS _factor retirement_yretirement_y ear ear_CBI

FALSE 1 653 4 N 2013 FALSE

FALSE 1 2415 17.5 N FALSE

FALSE 1 2458 18.9 N FALSE

Page 22
boiler_information

NOx_controlSO2_controlcombustion_additives

No Yes No

Yes Yes No

Yes Yes No

Page 23
boiler_fuels

facility_id boiler_id fuel_type fuel_year percentage_massvol percentage_btu other_type

3992 7 coal - bituminous2007 0 83

3992 7 coal - bituminous2008 0 86

3992 7 coal - bituminous2009 0 23

3992 7 natural gas 2007 0 17

3992 7 natural gas 2008 0 14

3992 7 natural gas 2009 0 77

3992 8 coal - bituminous2007 0 88

3992 8 coal - bituminous2008 0 91

3992 8 coal - bituminous2009 0 84

3992 8 natural gas 2007 0 8

3992 8 natural gas 2008 0 7

3992 8 natural gas 2009 0 16

3992 8 other non-fossil fuel (specify 2007 ) 0 4 Paper derived fuel

3992 8 other non-fossil fuel (specify 2008 ) 0 2 Paper derived fuel

3992 9 coal - bituminous2007 0 91

3992 9 coal - bituminous2008 0 94

3992 9 coal - bituminous2009 0 86

3992 9 natural gas 2007 0 7

3992 9 natural gas 2008 0 5

3992 9 natural gas 2009 0 14

3992 9 other non-fossil fuel (specify 2007 ) 0 2 Paper derived fuel

3992 9 other non-fossil fuel (specify 2008 ) 0 1 Paper derived fuel

Page 24
boiler_control_NOx

facility_id boiler_id NOx_type NOx_other NOx_online

3992 8 Other (specify Modified burners ) 4/1/1997

3992 9 Other (specify Modified burners ) 4/1/1999

Page 25
boiler_control_SO2

facility_id boiler_id SO2_type SO2_other SO2_online

3992 7 Low Sulfur Coal 1/1/1984

3992 8 Low Sulfur Coal 1/1/1984

3992 9 Low Sulfur Coal 1/1/1984

Page 26
boiler_additives

facility_id boiler_id boiler_additive additive_other additive_online

Page 27
facility_units

facility_id unit_id

3992 1345T

3992 6T

3992 7T

Page 28
unit_boilers

facility_id unit_id boiler_id

3992 1345T 7

3992 6T 8

3992 7T 9

Page 29
facility_controls

facility_id control_id control_groupcontrol_typecontrol_otherlegacy_control cntrol_onlinecontrol_offlineNOx_reagent

3992 ESP7 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1975

3992 ESP8 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1973

3992 ESP9 PM control Electrostatic precipitator, cold side, w/o flue gas conditioning FALSE 1/1/1973

3992 MC7 PM control Multiple cyclone FALSE 12/1/1949

3992 MC8 PM control Multiple cyclone FALSE 6/1/1957

3992 MC9 PM control Multiple cyclone FALSE 7/1/1961

Page 30
facility_controls

reagent_other NOx_ammonia SO2_sorbent oher_sorbent SO2_scrubber_additive

Page 31
facility_sampling_ports

facility_id sampling_port_id

3992 7-1

3992 7-2

3992 7-3

3992 7-4

3992 7-5

3992 8-1

3992 8-2

3992 8-3

3992 8-4

3992 8-5

3992 9-1

3992 9-2

3992 9-3

3992 9-4

3992 9-5

Page 32
facility_stacks

facility_id stack_id stack_heightstack_diameter sack_gas_velocity

3992 S14 250 10.5 23.4

3992 S15 250 8.5 72.4

3992 S16 250 8.5 70

Page 33
configurations

facility_id configuration_id

3992 7B1345T

3992 8B6T

3992 9B7T

Page 34
configuration_components

facility_id configuration_id component_idorder component_ty port_near pe

3992 7B1345T 1345T 1 Unit

3992 7B1345T 7-1 4 Sampling Port pevious

3992 7B1345T 7-2 5 Sampling Port pevious

3992 7B1345T 7-3 6 Sampling Port pevious

3992 7B1345T 7-4 7 Sampling Port pevious

3992 7B1345T 7-5 8 Sampling Port pevious

3992 7B1345T ESP7 3 PM control

3992 7B1345T MC7 2 PM control

3992 7B1345T S14 9 Stack

3992 8B6T 6T 1 Unit

3992 8B6T 8-1 4 Sampling Port pevious

3992 8B6T 8-2 5 Sampling Port pevious

3992 8B6T 8-3 6 Sampling Port pevious

3992 8B6T 8-4 7 Sampling Port pevious

3992 8B6T 8-5 8 Sampling Port pevious

3992 8B6T ESP8 3 PM control

3992 8B6T MC8 2 PM control

3992 8B6T S15 9 Stack

3992 9B7T 7T 1 Unit

3992 9B7T 9-1 4 Sampling Port pevious

3992 9B7T 9-2 5 Sampling Port pevious

3992 9B7T 9-3 6 Sampling Port pevious

3992 9B7T 9-4 7 Sampling Port pevious

3992 9B7T 9-5 8 Sampling Port pevious

3992 9B7T ESP9 3 PM control

3992 9B7T MC9 2 PM control

3992 9B7T S16 9 Stack

Page 35
configuration_pollutants1

facility_id configuration_id pollutant_nampermit_ty e pe_1emlimit_1 emlimit_units_1 avg_period_1emlimit_2 emlimit_units_2

3992 8B6T Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.46 pound per million British Thermal Unit (lb/MMBtu) 24 hours

3992 9B7T PM (Condensable) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu) 1 hour

3992 9B7T Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.46 pound per million British Thermal Unit (lb/MMBtu) 24 hours

3992 9B7T Sulfur Dioxide (SO2) Federal - Title V Operating Permit 4.25 pound per million British Thermal Unit (lb/MMBtu) 24 hours

3992 7B1345T PM (Condensable) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu) 1 hour

3992 7B1345T Sulfur Dioxide (SO2) Federal - Title V Operating Permit 4.25 pound per million British Thermal Unit (lb/MMBtu) 24 hours

3992 7B1345T Nitrogen Oxide (NOx) Federal - Title V Operating Permit 0.68 pound per million British Thermal Unit (lb/MMBtu) 24 hours

3992 8B6T PM (Condensable) Federal - Title V Operating Permit 0.6 pound per million British Thermal Unit (lb/MMBtu) 1 hour

3992 8B6T Sulfur Dioxide (SO2) Federal - Title V Operating Permit 4.25 pound per million British Thermal Unit (lb/MMBtu) 24 hours

Page 36
configuration_pollutants1

avg_period_2emlimit_details test_methodemrate emrate_unitsguarantee_level_explainreq_monitoringeq_recordkeeping

CEM based averaging period 0 pound per million British Thermal Unit (lb/MMBtu) No NA - Calibrate, maintain and operate a continuous - The continuous monitor shall perf

Emission tests required every EPA Method 5 24 months. A waiver may 0 pound per million British Thermal Unit (lb/MMBtu) No be approved if testing demonstrates that PM emissions arNA - Emission testing required every - Retain copies of emission tests. 24 months. 

CEM based averaging period 0 pound per million British Thermal Unit (lb/MMBtu) No NA - Calibrate, maintain and operate a continuous - The continuous monitor shall perf

CEM based averaging period 0 pound per million British Thermal Unit (lb/MMBtu) No NA - Calibrate, maintain and operate a continuous - The continuous monitor shall perf

Compliance testing required every EPA Method 5 0 24 months. A waiver may pound per million British Thermal Unit (lb/MMBtu) No NA be requested if the results of testing demonstrate that - Emission testing required every - Retain copies of emission tests. 24 months. 

CEM based averaging period 0 pound per million British Thermal Unit (lb/MMBtu) No NA - Calibrate, maintain and operate a continuous - The continuous monitor shall perf

CEM based averaging period 0 pound per million British Thermal Unit (lb/MMBtu) No NA - Calibrate, maintain and operate a continuous - The continuous monitor shall perf

Emission tests required every EPA Method 5 24 months. A waiver may 0 pound per million British Thermal Unit (lb/MMBtu) No be approved if testing demonstrates that PM emissions are NA - Emission testing required every - Retain copies of emission tests. 24 months. 

CEM based averaging period 0 pound per million British Thermal Unit (lb/MMBtu) No NA - Calibrate, maintain and operate a continuous - The continuous monitor shall perf

Page 37
configuration_pollutants1

req_reporting

- Submit quarterly excess emission reports within 30 days following the end of each calendar quarter.

- Retain copies of emission tests.- Keep monthly records of types and amounts of fuels fired in the boiler and heat inputs of alternate fu

- Submit quarterly excess emission reports within 30 days following the end of each calendar quarter.

- Submit quarterly excess emission reports within 30 days following the end of each calendar quarter.

- Retain copies of emission tests.- Keep monthly records of types and amounts of fuels fired in the boiler.- Record control equipmen

- Submit quarterly excess emission reports within 30 days following the end of each calendar quarter.

- Submit quarterly excess emission reports within 30 days following the end of each calendar quarter.

- Retain copies of emission tests.- Keep monthly records of types and amounts of fuels fired in the boiler and heat inputs of alternate fu

- Submit quarterly excess emission reports within 30 days following the end of each calendar quarter.

Page 38
configuration_pollutants1

 boiler and heat inputs of alternate fuels used.- Record control equipment parameters at least once every 8 hours of operation.- Keep 

 boiler.- Record control equipment parameters at least once every 8 hours of operation.- Keep annual records of inspections on contro

 boiler and heat inputs of alternate fuels used.- Record control equipment parameters at least once every 8 hours of operation.- Keep 

Page 39
configuration_pollutants1

very 8 hours of operation.- Keep annual records of inspections on control equipment.- Keep records of boiler inspections.- Keep m

nual records of inspections on control equipment.- Keep records of boiler inspections.

very 8 hours of operation.- Keep annual records of inspections on control equipment.- Keep records of boiler inspections.- Keep m

Page 40
configuration_pollutants1

rds of boiler inspections.- Keep monthly records of total average percentage of heat input supplied from all alternate fuels combined.- 

rds of boiler inspections.- Keep monthly records of total average percentage of heat input supplied from all alternate fuels combined.- 

Page 41
configuration_pollutants1

rom all alternate fuels combined.- Keep specific operating parameter records each time paper derived fuel is fired.- Keep specific reco

rom all alternate fuels combined.- Keep specific operating parameter records each time paper derived fuel is fired.- Keep specific reco

Page 42
configuration_pollutants1

d fuel is fired.- Keep specific records for each batch of paper derived fuel.

d fuel is fired.- Keep specific records for each batch of paper derived fuel.

Page 43
control_technologies

facility_id configuration_id component_idcontrol_id project_titleproject_typevendor_namevndor_contact vendor_phone

Page 44
control_technologies

vendor_address vndor_cityvendor_statevendor_zip actual_start_date projected_start_date end_date sorbent chemical_additive

Page 45
control_technologies

injection_point HAP_emission_reduction HAP_emission_rate HAP_emission_rate_units HAP_achieved_reduction HAP_achieved_rate HAP_achieved_rate_units feed_rate feed_rate_units

Page 46
control_technologies

feed_rate_units

Page 47
control_coal_ranks

facility_id configuration_id component_idcontrol_id coal_type

Page 48
control_pollutants1

facility_id configuration_id component_idcontrol_id pollutant_name

Page 49
control_costs

facility_id configuration_id component_idcontrol_id boiler_retrofit boiler_new_install total_capital_investm total_operating_costs entbase_year

Page 50
control_costs

CBI

Page 51
misc_controls

facility_id misc_control_id control_description

3992 1 Hydrogen chloride: The chlorine content in paper derived fuel may not exceed 18,800 ppm by weight. T

3992 2 Nickel: The total amount of paper derived fuel used at the facility may not exceed 1229 tons per month 

3992 3 Particulate emissions: Alternate fuels may not be burned in quantities greater than the lesser of 30% he

3992 4 Hazardous air contaminants: Good combustion technology for wood fuels.

Page 52
misc_controls

not exceed 18,800 ppm by weight. The heat content of the paper derived fuel shall be greater than or equal to 5500 Btu/lb. Each batch of fu

ay not exceed 1229 tons per month averaged over 12 months. The concentration of nickel in the paper derived fuel may not exceed 150 pp

es greater than the lesser of 30% heat input supplied to the boiler or the percentage, in heat input supplied by wood fuel during the most rec

Page 53
misc_controls

qual to 5500 Btu/lb. Each batch of fuel is sampled.

 derived fuel may not exceed 150 ppm by weight. Each batch is sampled.

ied by wood fuel during the most recent stack test.

Page 54
misc_control_configurations

facility_id misc_control_id configuration_id

3992 1 8B6T

3992 1 9B7T

3992 2 8B6T

3992 2 9B7T

3992 3 8B6T

3992 3 9B7T

3992 4 8B6T

3992 4 9B7T

Page 55
fuel_shipments

facility_id shipment_idshipment_date amount_received amount_unitsfuel_type state_countryother_countrycounty

Page 56
fuel_shipments

coal_seam shipment_method

Page 57
fuel_shipment_configurations

facility_id shipment_idconfiguration_id

Page 58
fuel_shipment_samples

facility_id shipment_idsample_id amount_fuelamount_fuel_units total_sulfur ash_contentheating_valuehating_units

Page 59
fuel_shipment_samples

chlorine chlorine_unitsfluorine fluorine_unitsdata_provideddata_other_specified supplier_typesupplier_name supplier_address

Page 60
fuel_shipment_samples

supplier_citysupplier_statesupplier_ziplab_name lab_addresslab_city lab_state lab_zip analysis_copies

Page 61
fuel_shipment_samples

analysis_copies

Page 62
fuel_sample_pollutants

facility_id shipment_idsample_id fuel_pollutant pollutant_conc pollutant_conc_units pollutant_conc_ND pollutant_conc_MDL

Page 63
test_reports

facility_id report_id report_typeother_type report_description report_begin_date report_end_date before_control during_deviation

3992 M074302 compliance Total particulate emissions test during full load operating conditions. ######## No No

3992 M083603 compliance Total particulate emissions test during full load operating conditions. 9/3/2008 No No

3992 M083808 compliance Total particulate emissions test during full load operating conditions. 9/18/2008 9/19/2008 No No

Page 64
test_reports

deviation_reports

No

No

No

Page 65
test_report_configurations

facility_id report_id configuration_id

3992 M074302 7B1345T

3992 M083603 9B7T

3992 M083808 8B6T

Page 66
test_report_fuels

facility_id report_id fuel_id

3992 M074302 Coal

3992 M083603 Coal/pdf

3992 M083808 Coal/pdf

Page 67
test_report_fuel_types

facility_id report_id fuel_id fuel_type percentage_massvol percentage_btu other_type

3992 M074302 Coal coal - bituminous 100 100

3992 M083603 Coal/pdf coal - bituminous 94.3 91.3

3992 M083603 Coal/pdf other non-fossil fuel (specify 5.7 ) 8.7 Paper-derived fuel

3992 M083808 Coal/pdf coal - bituminous 95.6 95.6

3992 M083808 Coal/pdf other non-fossil fuel (specify 4.4 ) 4.4 Paper Derived Fuel

Page 68
cem_data

facility_id time_periodcem_period_description

3992 January 2005 - February 2010

Page 69
cem_data_pollutants1

facility_id time_periodpollutant_name

3992 January 2005 - February Sulfur Dioxide (SO2) 2010

3992 January 2005 - February Nitrogen Oxide (NOx) 2010

Page 70
test_report_sampling

facility_id report_id sampling_port_id point_differpoint_description befre_SO2_device point_orientation normal_bypass_percent testing_bypass_percent

3992 M074302 S14 No No

3992 M083603 S16 No No

3992 M083808 S15 No No

Page 71
test_report_sampling

fg_fraction

Page 72
sampling_runs

facility_id report_id sampling_port_id run_id start_datetime end_datetimunit_load e net_generation fg_moisture_content

3992 M074302 S14 1 ######## ######## 25 40.2 6.9

3992 M074302 S14 2 ######## ######## 26 38.7 7.3

3992 M074302 S14 3 ######## ######## 26 51.2 7.9

3992 M083603 S16 1 9/3/2008 9/3/2008 51 60.3 8

3992 M083603 S16 2 9/3/2008 9/3/2008 51 59.9 8.3

3992 M083603 S16 3 9/3/2008 9/3/2008 48 56.8 8.5

3992 M083808 S15 1 9/18/2008 9/18/2008 45 50 7

3992 M083808 S15 2 9/18/2008 9/18/2008 46 65.1 6.5

3992 M083808 S15 3 9/19/2008 9/19/2008 46 66.4 7.4

Page 73
sampling_runs

fg_flow_ratefg_flow_rate_units standard_temperature standard_pressure normal_temperature normal_pressure fg_oxygen_content fg_CO2_content fg_temperature

68920 dscfm 68 1 6 13 1

70567 dscfm 68 1 5.5 12.5 1

71857 dscfm 68 1 6.5 12 1

144154 dscfm 68 1 7.1 12.5 1

144441 dscfm 68 1 6.8 12.8 1

141942 dscfm 68 1 6.7 12.7 300

153893 dscfm 68 1 8.6 10.4 1

154924 dscfm 68 1 8.1 10.8 1

153246 dscfm 68 1 8.5 10.7 1

Page 74
sampling_runs

fg_pressureHg_loi test_methodrun_comments fuel_id fuel_unit_loadfuel_flow_ratefuel_ash fuel_heating_value

0.96 Methods 1, 2, 3A, 5, and 202 None Coal 25 30641.9 11.12 12626

0.96 Methods 1, 2, 3A, 5, and 202 None Coal 26 33026.3 11.02 12773

0.96 Methods 1, 2, 3A, 5, and 202 Sootblowing conducted during this run Coal 26 33140.9 10.06 13077

0.98 Methods 1, 2, 3, 5 and 202. None Coal/pdf 51 54575 10.57 12193

0.98 Methods 1, 2, 3, 5 and 202. None Coal/pdf 51 56552 11.52 13101

0.98 Methods 1, 2, 3, 5 and 202. Sootblowing conducted during this run. Coal/pdf 48 54575 11.83 13188

1 Methods 1, 2, 3A, 5, and 202 None Coal/pdf 45 51829 10.99 13067

1 Methods 1, 2, 3A, 5, and 202 None Coal/pdf 46 50179 10.8 12604

1 Methods 1, 2, 3A, 5, and 202 Sootblowing conducted during this test run. Coal/pdf 46 50474 10.52 12868

Page 75
sampling_runs

fuel_sulfur

1.31

1.43

1.24

1.44

1.65

1.55

1.59

1.71

1.58

Page 76
sampling_run_pollutants1

facility_id report_id sampling_port_id run_id pollutant_namconce conc_units conc_ND conc_MDL

3992 M074302 S14 1 PM (Filterable) 0.0013 FALSE

3992 M074302 S14 1 PM (Condensable) 0.0025 FALSE

3992 M074302 S14 2 PM (Filterable) 0.0025 FALSE

3992 M074302 S14 2 PM (Condensable) 0.0065 FALSE

3992 M074302 S14 3 PM (Filterable) 0.0079 FALSE

3992 M074302 S14 3 PM (Condensable) 0.0023 FALSE

3992 M083808 S15 1 PM (Filterable) 0.0478 FALSE

3992 M083808 S15 1 PM (Condensable) 0.0136 FALSE

3992 M083808 S15 2 PM (Filterable) 0.0932 FALSE

3992 M083808 S15 2 PM (Condensable) 0.0119 FALSE

3992 M083808 S15 3 PM (Filterable) 0.0466 FALSE

3992 M083808 S15 3 PM (Condensable) 0.0228 FALSE

3992 M083603 S16 1 PM (Filterable) 0.0351 FALSE

3992 M083603 S16 1 PM (Condensable) 0.0102 FALSE

3992 M083603 S16 2 PM (Filterable) 0.0268 FALSE

3992 M083603 S16 2 PM (Condensable) 0.0411 FALSE

3992 M083603 S16 3 PM (Filterable) 0.0266 FALSE

3992 M083603 S16 3 PM (Condensable) 0.0153 FALSE

Page 77
sampling_run_pollutants1

emission_rateemission_rate_units emission_rate_ND emission_rate_MDL emission_factor emission_factor_units emission_factor_ND emission_factor_MDL run_pollutant_comment

0.741 pound per hour (lb/hr) FALSE 0.0026 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

1.467 pound per hour (lb/hr) FALSE 0.0051 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

1.532 pound per hour (lb/hr) FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

3.954 pound per hour (lb/hr) FALSE 0.013 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

4.889 pound per hour (lb/hr) FALSE 0.0168 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

1.443 pound per hour (lb/hr) FALSE 0.005 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

63.115 pound per hour (lb/hr) FALSE 0.1119 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

17.95 pound per hour (lb/hr) FALSE 0.0318 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

123.758 pound per hour (lb/hr) FALSE 0.2122 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

15.85 pound per hour (lb/hr) FALSE 0.0272 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

61.153 pound per hour (lb/hr) FALSE 0.109 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

29.9 pound per hour (lb/hr) FALSE 0.0533 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

43.345 pound per hour (lb/hr) FALSE 0.074 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

12.61 pound per hour (lb/hr) FALSE 0.0215 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

33.173 pound per hour (lb/hr) FALSE 0.0554 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

50.84 pound per hour (lb/hr) FALSE 0.0849 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

32.342 pound per hour (lb/hr) FALSE 0.053 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

18.59 pound per hour (lb/hr) FALSE 0.0305 pound per million British Thermal Unit (lb/MMBtu) FALSE Concentration Units: grains/dscf

Page 78
sampling_run_pollutants1

run_pollutant_comment

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Concentration Units: grains/dscf

Page 79
sampling_run_fuel

facility_id report_id sampling_port_id run_id fuel_pollutant fuel_conc fuel_conc_units fuel_conc_NDfuel_conc_MDL

Page 80
sampling_run_fuel

fuel_conc_MDL

Page 81