### Name:

Title: Company: Sign Date: Name: Title: Company: Sign Date: Permitted Facility Representative / Date Testing Company Representative / Date Final Test Report for

/ / Based on information and belief formed after reasonable inquiry, I certify that the statements and information in this test report are true, accurate, and complete. I have reviewed all testing details and results in this test report and hereby certify that the test report is authentic and accurate.

Friday, February 11, 2011 Page 1 of 33

### Facility Information:

ENTERGY MS BAXTER WILSON POWE 770 Kemp Bottom Road

Vicksburg MS 39180 Contact: Theordore Chenet
Phone: 281-297-3313
Fax: 281-297-3013
Email: TCHENET@entergy.com Testing Company:
METCO Environmental
3226 Commander Blvd.

Carrollton TX 75006 Contact: Ned Shappley
Phone: 972-931-7127
Fax: 972-931-8398
Email: nshappley@metcoenv.com

Air Permit Number: Permitted Source ID/Name: Unit Number 1 Stack Boiler ID
Permitted Maximum Process Rate: N/A Max. Normal Operation Process Rate: N/A Target Process Test Rate N/A

Description of the source (including control equipment). Please see the attachments for source or process flow diagram: This description should describe the process and associated controls to differentiate this facility from, or document similarity with others of same SCC. Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information: AFS #: 110000376548 FRS #: 110000376548

SCC / Description 10102101 External Combustion Boilers - Electric Generation - Other Oil - All

The following state and federal regulations that apply to the proposed testing:

Location Round

Duct Diam. Distance from upstream dist. Distance from

downstream dist. Number of

Traverse Ports Equiv. Diam Min.Travers Points Rect. Duct Length /Width
Stack Exit 228 2508 2280 4 228 12 0 0
Exhaust Duct 0 152 196 1 304 3 216 512

Target Parameter Test Method Number of

Test Runs Test Run

Duration Sample

Points Comments Location
Carbon Monoxide Method 10 3 420 0 Stack Exit 2,3,7,8-TCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0 Stack Exit



### Friday, February 11, 2011 Page 2 of 331,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0 Stack Exit 2,3,7,8-TCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0 Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0 Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0 Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0 Stack Exit OCDF Method 23 3 480 0 Stack Exit Other TCDD Method 23 3 480 0 Stack Exit Other PeCDD Method 23 3 480 0 Stack Exit Other HxCDD Method 23 3 480 0 Stack Exit Other HpCDD Method 23 3 480 0 Stack Exit Other TCDF Method 23 3 480 0 Stack Exit Other PeCDF Method 23 3 480 0 Stack Exit Other HxCDF Method 23 3 480 0 Stack Exit Other HpCDF Method 23 3 480 0 Stack Exit Total Dioxins Method 23 3 480 0 Stack Exit Total Furans Method 23 3 480 0 Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0 Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0 Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0 Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0 Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0 Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0 Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0 Stack Exit 2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157) Method 23 3 480 0 Stack Exit

2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0 Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0 Stack Exit 2,3,3',4,4',5,5'-HpCB

(PCB189) Method 23 3 480 0 Stack Exit

Total organic compounds

(TOC) as Propane Method 25A 3 180 0 Stack Exit

Inorganic (Aqueous)

Condensible Part. OTM - 27/28 3 366 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Filterable PM2.5 OTM - 27/28 3 366 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Organic Condensible

Particulate OTM - 27/28 3 366 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Total PM2.5 OTM - 27/28 3 366 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Total Particulate OTM - 27/28 3 366 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit



### Friday, February 11, 2011 Page 3 of 33

### The following describes any modifications and/or deviations to the applicable test

methods. If alternative methods were requested, see the attachments for documentation of request AND approval, including dates. Two of the test ports at the stack were unable to be sampled out of due to testing location obstructions. The samples were taken out of the two available test ports. Six total points were sampled out of the two existing ports.
Method 26 was modified to collect HCN with the HCL and HF.The concentration of the sodium hydroxide solution used was increased from 0.1 N to 6N , an additional impinger containing sodium hydroxide was added to the train (three impingers instead of two), the pH of the impinger solutions was monitored periodically throughout the sample run. This modification was addressed on the Uticility ICR website in the Frequently Asked Questions area (Question Test-025). At the time of testing, this modification was still approved.
The reference method monitors, HCL, HF, HCN, and VOST sampling was performed at the Exhaust Outlet Duct located at the base of the stack. The sampling ports used were directly above the plant CEMS monitor location.

Filterable Particulate OTM - 27/28 3 366 0 Use only for dry stacks. Delete Method 5/OTM28 tests. Stack Exit

Filterable Particulate Method 29 3 240 0 Stack Exit Beryllium Method 29 3 240 0 Stack Exit Cadmium Method 29 3 240 0 Stack Exit Chromium Method 29 3 240 0 Stack Exit Lead Method 29 3 240 0 Stack Exit Mercury Method 29 3 240 0 Stack Exit Selenium Method 29 3 240 0 Stack Exit Phosphorus (yellow or white) Method 29 3 240 0 Stack Exit Antimony Method 29 3 240 0 Stack Exit Cobalt Method 29 3 240 0 Stack Exit Manganese Method 29 3 240 0 Stack Exit Arsenic Method 29 3 240 0 Stack Exit Nickel Method 29 3 240 0 Stack Exit Co2 Method 3A CO2 3 420 0 Stack Exit O2 Method 3A O2 3 420 0 Stack Exit Sulfur Dioxide Method 6C 3 420 0 Stack Exit Nitrogen oxides (NOx) Method 7E 3 420 0 Stack Exit



### Friday, February 11, 2011 Page 4 of 33

### Sampling / Stack Data Results Summary



### Location Stack Exit - Method 10 Average
Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Stack Exit - Method 23 Average Run Number 1 2 3
Test Date 5/11/2010 5/12/2010 5/12/2010
Run Start Time 2:12:00 PM 7:25:00 AM 2:35:00 AM

Run Finish Time 11:50:00 PM 3:34:00 PM 1/1/1900 2:15:00 AM Net Run Time, minutes 480 480 480 Dry Gas Meter Volume Sampled, dscf 315.388 322.762 297.956 312.035 Moisture Content of Stack Gas, % 9.07 9.89 10.12 9.693 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Carbon Dioxide, % 10.5 10.4 10.5 10.467 Oxygen, % 7.7 7.6 7.7 7.667 Average Stack Gas Temperature, °F 219.63 232.44 225.94 226.003 Dry Volumetric Flow Rate, dry scfm 812,312.6 795,401.1 775,118.8 794,277.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,164,283.5 1,169,727.2 1,132,471.5 1,155,494.06 7 Percent Isokinetic of Sampling Rate, % 99.1 103.6 98.1 100.267 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000
Fw 10320 10320 10320 10,320.000
Fc 1420 1420 1420 1,420.000



### Friday, February 11, 2011 Page 5 of 33

### Location Stack Exit - Method 25A Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Stack Exit - Method 29 Average Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Friday, February 11, 2011 Page 6 of 33

### Location Stack Exit - Method 3A CO2 Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Stack Exit - Method 3A O2 Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Friday, February 11, 2011 Page 7 of 33

### Location Stack Exit - Method 6C Average

Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Location Stack Exit - Method 7E Average Run Number
Test Date
Run Start Time
Run Finish Time Carbon Dioxide, % Oxygen, % Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Fuel Type
Fw
Fc



### Friday, February 11, 2011 Page 8 of 33

### Location Stack Exit - OTM - 27/28 Average

Run Number
Test Date
Run Start Time
Run Finish Time Net Run Time, minutes Dry Gas Meter Volume Sampled, dscf Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Carbon Dioxide, % Oxygen, % Average Stack Gas Temperature, °F Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % F-Factor, dscfm/MMBtu @ %O2
Fw
Fc



### Friday, February 11, 2011 Page 9 of 33

### Emissions Summary



### Location: Stack Exit - Method 10 Compound: Carbon Monoxide Average Run 1 2 3 Elb/hr 0.00E+00 0.00E+00 -1.12E+00 -0.373 lb/mmBtuO2 0.00E+00 0.00E+00 -3.37E-04 0.000 ppm 0.00E+00 0.00E+00 -3.19E-01 -0.106 ppm@7%O2 0.00E+00 0.00E+00 -3.35E-01 -0.112



### Location: Stack Exit - Method 23 Compound: 1,2,3,4,6,7,8-HpCDD Average RunNumber 1 2 3 Mass_mg 0.0000000072 0.0000000057 0.0000000043 0.000 Elb/hr 2.45E-09 1.86E-09 1.48E-09 0.000 lb/mmBtuO2 7.32E-13 5.62E-13 4.63E-13 0.000 ng/dscm 8.06E-04 6.24E-04 5.10E-04 0.001 ng/dscm@7%O2 8.49E-04 6.52E-04 5.37E-04 0.001


### Compound: 1,2,3,4,6,7,8-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000042 0.0000000063 0.000000004 0.000 Elb/hr 1.43E-09 2.05E-09 1.38E-09 0.000 lb/mmBtuO2 4.27E-13 6.21E-13 4.31E-13 0.000 ng/dscm 4.70E-04 6.89E-04 4.74E-04 0.001 ng/dscm@7%O2 4.95E-04 7.20E-04 4.99E-04 0.001


### Compound: 1,2,3,4,7,8,9-HpCDF Average RunNumber 1 2 3 Mass_mg 0.0000000027 0.0000000034 0.0000000018 0.000 Elb/hr 9.20E-10 1.11E-09 6.19E-10 0.000 lb/mmBtuO2 2.75E-13 3.35E-13 1.94E-13 0.000 ng/dscm 3.02E-04 3.72E-04 2.13E-04 0.000 ng/dscm@7%O2 3.18E-04 3.89E-04 2.24E-04 0.000


### Compound: 1,2,3,4,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000017 0.000000002 0.0000000013 0.000 Elb/hr 5.79E-10 6.52E-10 4.47E-10 0.000 lb/mmBtuO2 1.73E-13 1.97E-13 1.40E-13 0.000 ng/dscm 1.90E-04 2.19E-04 1.54E-04 0.000 ng/dscm@7%O2 2.00E-04 2.29E-04 1.62E-04 0.000


### Compound: 1,2,3,4,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000028 0.000000004 0.0000000022 0.000 Elb/hr 9.54E-10 1.30E-09 7.57E-10 0.000



### Friday, February 11, 2011 Page 10 of 33lb/mmBtuO2 2.85E-13 3.95E-13 2.37E-13 0.000 ng/dscm 3.14E-04 4.38E-04 2.61E-04 0.000 ng/dscm@7%O2 3.31E-04 4.58E-04 2.75E-04 0.000


### Compound: 1,2,3,6,7,8-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000017 0.0000000019 0.0000000013 0.000 Elb/hr 5.79E-10 6.19E-10 4.47E-10 0.000 lb/mmBtuO2 1.73E-13 1.87E-13 1.40E-13 0.000 ng/dscm 1.90E-04 2.08E-04 1.54E-04 0.000 ng/dscm@7%O2 2.00E-04 2.17E-04 1.62E-04 0.000


### Compound: 1,2,3,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000022 0.0000000018 0.0000000008 0.000 Elb/hr 7.50E-10 5.87E-10 2.75E-10 0.000 lb/mmBtuO2 2.24E-13 1.78E-13 8.61E-14 0.000 ng/dscm 2.46E-04 1.97E-04 9.48E-05 0.000 ng/dscm@7%O2 2.59E-04 2.06E-04 9.98E-05 0.000


### Compound: 1,2,3,7,8,9-HxCDD Average RunNumber 1 2 3 Mass_mg 0.0000000017 0.000000002 0.0000000013 0.000 Elb/hr 5.79E-10 6.52E-10 4.47E-10 0.000 lb/mmBtuO2 1.73E-13 1.97E-13 1.40E-13 0.000 ng/dscm 1.90E-04 2.19E-04 1.54E-04 0.000 ng/dscm@7%O2 2.00E-04 2.29E-04 1.62E-04 0.000


### Compound: 1,2,3,7,8,9-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000033 0.0000000014 0.00000000084 0.000 Elb/hr 1.12E-09 4.56E-10 2.89E-10 0.000 lb/mmBtuO2 3.36E-13 1.38E-13 9.04E-14 0.000 ng/dscm 3.70E-04 1.53E-04 9.96E-05 0.000 ng/dscm@7%O2 3.90E-04 1.60E-04 1.05E-04 0.000


### Compound: 1,2,3,7,8-PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000043 0.0000000048 0.0000000015 0.000 Elb/hr 1.46E-09 1.56E-09 5.16E-10 0.000 lb/mmBtuO2 4.37E-13 4.73E-13 1.61E-13 0.000 ng/dscm 4.82E-04 5.25E-04 1.78E-04 0.000 ng/dscm@7%O2 5.08E-04 5.49E-04 1.87E-04 0.000


### Compound: 1,2,3,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000044 0.0000000045 0.0000000012 0.000 Elb/hr 1.50E-09 1.47E-09 4.13E-10 0.000



### Friday, February 11, 2011 Page 11 of 33lb/mmBtuO2 4.48E-13 4.44E-13 1.29E-13 0.000 ng/dscm 4.93E-04 4.92E-04 1.42E-04 0.000 ng/dscm@7%O2 5.19E-04 5.14E-04 1.50E-04 0.000


### Compound: 2,3,3',4,4',5,5'-HpCB (PCB189) Average RunNumber 1 2 3 Mass_mg 0.0000000161 0.0000000148 0.0000000125 0.000 Elb/hr 5.49E-09 4.82E-09 4.30E-09 0.000 lb/mmBtuO2 1.64E-12 1.46E-12 1.35E-12 0.000 ng/dscm 1.80E-03 1.62E-03 1.48E-03 0.002 ng/dscm@7%O2 1.90E-03 1.69E-03 1.56E-03 0.002


### Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC Average RunNumber 1 2 3 Mass_mg 0.0000001036 0.0000000632 0.0000000472 0.000 Elb/hr 3.53E-08 2.06E-08 1.62E-08 0.000 lb/mmBtuO2 1.05E-11 6.23E-12 5.08E-12 0.000 ng/dscm 1.16E-02 6.92E-03 5.60E-03 0.008 ng/dscm@7%O2 1.22E-02 7.23E-03 5.90E-03 0.008


### Compound: 2,3,3',4,4'-PeCB (PCB105) Average RunNumber 1 2 3 Mass_mg 0.0000002318 0.0000000836 0.0000000234 0.000 Elb/hr 7.90E-08 2.73E-08 8.05E-09 0.000 lb/mmBtuO2 2.36E-11 8.25E-12 2.52E-12 0.000 ng/dscm 2.60E-02 9.15E-03 2.77E-03 0.013 ng/dscm@7%O2 2.74E-02 9.56E-03 2.92E-03 0.013


### Compound: 2,3',4,4',5,5'-HxCB (PCB167) Average RunNumber 1 2 3 Mass_mg 0.0000000179 0.0000000168 0.000000012 0.000 Elb/hr 6.10E-09 5.48E-09 4.13E-09 0.000 lb/mmBtuO2 1.82E-12 1.66E-12 1.29E-12 0.000 ng/dscm 2.00E-03 1.84E-03 1.42E-03 0.002 ng/dscm@7%O2 2.11E-03 1.92E-03 1.50E-03 0.002


### Compound: 2,3,4,4',5-PeCB (PCB114) Average RunNumber 1 2 3 Mass_mg 0.0000000152 0.0000000133 0.0000000113 0.000 Elb/hr 5.18E-09 4.34E-09 3.89E-09 0.000 lb/mmBtuO2 1.55E-12 1.31E-12 1.22E-12 0.000 ng/dscm 1.70E-03 1.46E-03 1.34E-03 0.002 ng/dscm@7%O2 1.79E-03 1.53E-03 1.41E-03 0.002


### Compound: 2,3',4,4',5-PeCB (PCB118) Average RunNumber 1 2 3 Mass_mg 0.0000006047 0.0000002175 0.0000000824 0.000 Elb/hr 2.06E-07 7.09E-08 2.84E-08 0.000



### Friday, February 11, 2011 Page 12 of 33lb/mmBtuO2 6.15E-11 2.15E-11 8.87E-12 0.000 ng/dscm 6.77E-02 2.38E-02 9.77E-03 0.034 ng/dscm@7%O2 7.13E-02 2.49E-02 1.03E-02 0.036


### Compound: 2',3,4,4',5-PeCB (PCB123) Average RunNumber 1 2 3 Mass_mg 0.0000000168 0.0000000148 0.0000000126 0.000 Elb/hr 5.72E-09 4.82E-09 4.34E-09 0.000 lb/mmBtuO2 1.71E-12 1.46E-12 1.36E-12 0.000 ng/dscm 1.88E-03 1.62E-03 1.49E-03 0.002 ng/dscm@7%O2 1.98E-03 1.69E-03 1.57E-03 0.002


### Compound: 2,3,4,6,7,8-HxCDF Average RunNumber 1 2 3 Mass_mg 0.0000000015 0.0000000016 0.00000000097 0.000 Elb/hr 5.11E-10 5.22E-10 3.34E-10 0.000 lb/mmBtuO2 1.53E-13 1.58E-13 1.04E-13 0.000 ng/dscm 1.68E-04 1.75E-04 1.15E-04 0.000 ng/dscm@7%O2 1.77E-04 1.83E-04 1.21E-04 0.000


### Compound: 2,3,4,7,8-PeCDF Average RunNumber 1 2 3 Mass_mg 0.0000000032 0.0000000025 0.0000000021 0.000 Elb/hr 1.09E-09 8.15E-10 7.23E-10 0.000 lb/mmBtuO2 3.25E-13 2.47E-13 2.26E-13 0.000 ng/dscm 3.58E-04 2.74E-04 2.49E-04 0.000 ng/dscm@7%O2 3.77E-04 2.86E-04 2.62E-04 0.000


### Compound: 2,3,7,8-TCDD Average RunNumber 1 2 3 Mass_mg 0.000000004 0.0000000046 0.0000000028 0.000 Elb/hr 1.36E-09 1.50E-09 9.64E-10 0.000 lb/mmBtuO2 4.07E-13 4.54E-13 3.01E-13 0.000 ng/dscm 4.48E-04 5.03E-04 3.32E-04 0.000 ng/dscm@7%O2 4.72E-04 5.26E-04 3.50E-04 0.000


### Compound: 2,3,7,8-TCDF Average RunNumber 1 2 3 Mass_mg 0.0000000031 0.0000000056 0.0000000017 0.000 Elb/hr 1.06E-09 1.83E-09 5.85E-10 0.000 lb/mmBtuO2 3.15E-13 5.52E-13 1.83E-13 0.000 ng/dscm 3.47E-04 6.13E-04 2.02E-04 0.000 ng/dscm@7%O2 3.65E-04 6.41E-04 2.13E-04 0.000


### Compound: 3,3',4,4',5,5'-HxCB (PCB169) Average RunNumber 1 2 3 Mass_mg 0.00000002 0.0000000183 0.0000000136 0.000 Elb/hr 6.81E-09 5.97E-09 4.68E-09 0.000



### Friday, February 11, 2011 Page 13 of 33lb/mmBtuO2 2.03E-12 1.81E-12 1.46E-12 0.000 ng/dscm 2.24E-03 2.00E-03 1.61E-03 0.002 ng/dscm@7%O2 2.36E-03 2.09E-03 1.70E-03 0.002


### Compound: 3,3',4,4',5-PeCB (PCB126) Average RunNumber 1 2 3 Mass_mg 0.0000000179 0.0000000146 0.0000000128 0.000 Elb/hr 6.10E-09 4.76E-09 4.40E-09 0.000 lb/mmBtuO2 1.82E-12 1.44E-12 1.38E-12 0.000 ng/dscm 2.00E-03 1.60E-03 1.52E-03 0.002 ng/dscm@7%O2 2.11E-03 1.67E-03 1.60E-03 0.002


### Compound: 3,3',4,4'-TCB (PCB77) Average RunNumber 1 2 3 Mass_mg 0.0000000758 0.0000000449 0.0000000153 0.000 Elb/hr 2.58E-08 1.46E-08 5.26E-09 0.000 lb/mmBtuO2 7.71E-12 4.43E-12 1.65E-12 0.000 ng/dscm 8.49E-03 4.91E-03 1.81E-03 0.005 ng/dscm@7%O2 8.94E-03 5.13E-03 1.91E-03 0.005


### Compound: 3,4,4',5-TCB (PCB81) Average RunNumber 1 2 3 Mass_mg 0.0000000185 0.0000000189 0.0000000146 0.000 Elb/hr 6.30E-09 6.16E-09 5.02E-09 0.000 lb/mmBtuO2 1.88E-12 1.86E-12 1.57E-12 0.000 ng/dscm 2.07E-03 2.07E-03 1.73E-03 0.002 ng/dscm@7%O2 2.18E-03 2.16E-03 1.82E-03 0.002


### Compound: OCDD Average RunNumber 1 2 3 Mass_mg 0.000000018 0.000000018 0.000000013 0.000 Elb/hr 6.13E-09 5.87E-09 4.47E-09 0.000 lb/mmBtuO2 1.83E-12 1.78E-12 1.40E-12 0.000 ng/dscm 2.02E-03 1.97E-03 1.54E-03 0.002 ng/dscm@7%O2 2.13E-03 2.06E-03 1.62E-03 0.002


### Compound: OCDF Average RunNumber 1 2 3 Mass_mg 0.000000011 0.0000000097 0.0000000056 0.000 Elb/hr 3.75E-09 3.16E-09 1.93E-09 0.000 lb/mmBtuO2 1.12E-12 9.57E-13 6.03E-13 0.000 ng/dscm 1.23E-03 1.06E-03 6.64E-04 0.001 ng/dscm@7%O2 1.30E-03 1.11E-03 6.99E-04 0.001


### Compound: Other HpCDD Average RunNumber 1 2 3 Mass_mg 0.000000014 0.0000000057 0.0000000043 0.000 Elb/hr 4.77E-09 1.86E-09 1.48E-09 0.000



### Friday, February 11, 2011 Page 14 of 33lb/mmBtuO2 1.42E-12 5.62E-13 4.63E-13 0.000 ng/dscm 1.57E-03 6.24E-04 5.10E-04 0.001 ng/dscm@7%O2 1.65E-03 6.52E-04 5.37E-04 0.001


### Compound: Other HpCDF Average RunNumber 1 2 3 Mass_mg 0.000000015 0.0000000063 0.000000004 0.000 Elb/hr 5.11E-09 2.05E-09 1.38E-09 0.000 lb/mmBtuO2 1.53E-12 6.21E-13 4.31E-13 0.000 ng/dscm 1.68E-03 6.89E-04 4.74E-04 0.001 ng/dscm@7%O2 1.77E-03 7.20E-04 4.99E-04 0.001


### Compound: Other HxCDD Average RunNumber 1 2 3 Mass_mg 0.000000037 0.000000037 0.000000027 0.000 Elb/hr 1.26E-08 1.21E-08 9.29E-09 0.000 lb/mmBtuO2 3.76E-12 3.65E-12 2.91E-12 0.000 ng/dscm 4.14E-03 4.05E-03 3.20E-03 0.004 ng/dscm@7%O2 4.36E-03 4.23E-03 3.37E-03 0.004


### Compound: Other HxCDF Average RunNumber 1 2 3 Mass_mg 0.000000035 0.000000017 0.000000015 0.000 Elb/hr 1.19E-08 5.54E-09 5.16E-09 0.000 lb/mmBtuO2 3.56E-12 1.68E-12 1.61E-12 0.000 ng/dscm 3.92E-03 1.86E-03 1.78E-03 0.003 ng/dscm@7%O2 4.13E-03 1.94E-03 1.87E-03 0.003


### Compound: Other PeCDD Average RunNumber 1 2 3 Mass_mg 0.0000000056 0.000000055 0.00000004 0.000 Elb/hr 1.91E-09 1.79E-08 1.38E-08 0.000 lb/mmBtuO2 5.70E-13 5.43E-12 4.31E-12 0.000 ng/dscm 6.27E-04 6.02E-03 4.74E-03 0.004 ng/dscm@7%O2 6.60E-04 6.29E-03 4.99E-03 0.004


### Compound: Other PeCDF Average RunNumber 1 2 3 Mass_mg 0.00000005 0.000000042 0.000000016 0.000 Elb/hr 1.70E-08 1.37E-08 5.51E-09 0.000 lb/mmBtuO2 5.09E-12 4.14E-12 1.72E-12 0.000 ng/dscm 5.60E-03 4.60E-03 1.90E-03 0.004 ng/dscm@7%O2 5.90E-03 4.81E-03 2.00E-03 0.004


### Compound: Other TCDD Average RunNumber 1 2 3 Mass_mg 0.000000035 0.000000037 0.000000024 0.000 Elb/hr 1.19E-08 1.21E-08 8.26E-09 0.000



### Friday, February 11, 2011 Page 15 of 33lb/mmBtuO2 3.56E-12 3.65E-12 2.58E-12 0.000 ng/dscm 3.92E-03 4.05E-03 2.84E-03 0.004 ng/dscm@7%O2 4.13E-03 4.23E-03 2.99E-03 0.004


### Compound: Other TCDF Average RunNumber 1 2 3 Mass_mg 0.000000023 0.000000036 0.000000017 0.000 Elb/hr 7.84E-09 1.17E-08 5.85E-09 0.000 lb/mmBtuO2 2.34E-12 3.55E-12 1.83E-12 0.000 ng/dscm 2.58E-03 3.94E-03 2.02E-03 0.003 ng/dscm@7%O2 2.72E-03 4.12E-03 2.13E-03 0.003


### Compound: Total Dioxins Average RunNumber 1 2 3 Mass_mg 0.0000001096 0.0000001527 0.0000001083 0.000 Elb/hr 3.73E-08 4.98E-08 3.73E-08 0.000 lb/mmBtuO2 1.11E-11 1.51E-11 1.17E-11 0.000 ng/dscm 1.23E-02 1.67E-02 1.28E-02 0.014 ng/dscm@7%O2 1.30E-02 1.75E-02 1.35E-02 0.015


### Compound: Total Furans Average RunNumber 1 2 3 Mass_mg 0.000000134 0.000000111 0.0000000576 0.000 Elb/hr 4.57E-08 3.62E-08 1.98E-08 0.000 lb/mmBtuO2 1.36E-11 1.09E-11 6.20E-12 0.000 ng/dscm 1.50E-02 1.21E-02 6.83E-03 0.011 ng/dscm@7%O2 1.58E-02 1.26E-02 7.19E-03 0.012



### Location: Stack Exit - Method 25A 

### Compound: Total organic compounds (TOC) as Average Run 1 2 3 Elb/hr 2.09E+00 0.00E+00 0.00E+00 0.697 lb/mmBtuO2 6.35E-04 0.00E+00 0.00E+00 0.000 ppm 3.77E-01 0.00E+00 0.00E+00 0.126 ppm@7%O2 4.02E-01 0.00E+00 0.00E+00 0.134



### Location: Stack Exit - Method 29 Compound: Antimony Average RunNumber 1 2 3 Mass_mg 0.229 0.2416 0.2116 0.227 Elb/hr 1.85E-01 1.94E-01 1.77E-01 0.185 lb/mmBtuO2 5.42E-05 5.92E-05 5.41E-05 0.000 mg/dscm 6.06E-02 6.52E-02 6.00E-02 0.062 mg/dscm@7%O2 6.29E-02 6.87E-02 6.27E-02 0.065


### Compound: Arsenic Average RunNumber 1 2 3



### Friday, February 11, 2011 Page 16 of 33Mass_mg 0.00929 0.01058 0.00848 0.009 Elb/hr 7.52E-03 8.50E-03 7.08E-03 0.008 lb/mmBtuO2 2.20E-06 2.59E-06 2.17E-06 0.000 mg/dscm 2.46E-03 2.85E-03 2.40E-03 0.003 mg/dscm@7%O2 2.55E-03 3.00E-03 2.51E-03 0.003


### Compound: Beryllium Average RunNumber 1 2 3 Mass_mg 0.001 0.001 0.001 0.001 Elb/hr 8.10E-04 8.03E-04 8.34E-04 0.001 lb/mmBtuO2 2.37E-07 2.45E-07 2.56E-07 0.000 mg/dscm 2.65E-04 2.70E-04 2.84E-04 0.000 mg/dscm@7%O2 2.75E-04 2.84E-04 2.97E-04 0.000


### Compound: Cadmium Average RunNumber 1 2 3 Mass_mg 0.0015 0.0015 0.0015 0.002 Elb/hr 1.21E-03 1.21E-03 1.25E-03 0.001 lb/mmBtuO2 3.55E-07 3.67E-07 3.83E-07 0.000 mg/dscm 3.97E-04 4.05E-04 4.25E-04 0.000 mg/dscm@7%O2 4.12E-04 4.26E-04 4.44E-04 0.000


### Compound: Chromium Average RunNumber 1 2 3 Mass_mg 0.02584 0.03101 0.00864 0.022 Elb/hr 2.09E-02 2.49E-02 7.21E-03 0.018 lb/mmBtuO2 6.12E-06 7.60E-06 2.21E-06 0.000 mg/dscm 6.84E-03 8.36E-03 2.45E-03 0.006 mg/dscm@7%O2 7.10E-03 8.80E-03 2.56E-03 0.006


### Compound: Cobalt Average RunNumber 1 2 3 Mass_mg 0.0453 0.0575 0.0441 0.049 Elb/hr 3.67E-02 4.62E-02 3.68E-02 0.040 lb/mmBtuO2 1.07E-05 1.41E-05 1.13E-05 0.000 mg/dscm 1.20E-02 1.55E-02 1.25E-02 0.013 mg/dscm@7%O2 1.24E-02 1.63E-02 1.31E-02 0.014


### Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 66.5 84.2 100.9 83.867 Elb/hr 5.39E+01 6.77E+01 8.42E+01 68.600 lb/mmBtuO2 1.57E-02 2.06E-02 2.58E-02 0.021 mg/dscm 1.76E+01 2.27E+01 2.86E+01 22.967 mg/dscm@7%O2 1.83E+01 2.39E+01 2.99E+01 24.033


### Compound: Lead Average RunNumber 1 2 3



### Friday, February 11, 2011 Page 17 of 33Mass_mg 0.01968 0.0217 0.01663 0.019 Elb/hr 1.59E-02 1.74E-02 1.39E-02 0.016 lb/mmBtuO2 4.66E-06 5.32E-06 4.25E-06 0.000 mg/dscm 5.21E-03 5.85E-03 4.72E-03 0.005 mg/dscm@7%O2 5.40E-03 6.16E-03 4.93E-03 0.005


### Compound: Manganese Average RunNumber 1 2 3 Mass_mg 0.01774 0.02224 0.01554 0.019 Elb/hr 1.44E-02 1.79E-02 1.30E-02 0.015 lb/mmBtuO2 4.20E-06 5.45E-06 3.97E-06 0.000 mg/dscm 4.69E-03 6.00E-03 4.41E-03 0.005 mg/dscm@7%O2 4.87E-03 6.32E-03 4.61E-03 0.005


### Compound: Mercury Average RunNumber 1 2 3 Mass_mg 0.00117 0.00116 0.00106 0.001 Elb/hr 9.47E-04 9.32E-04 8.84E-04 0.001 lb/mmBtuO2 2.77E-07 2.84E-07 2.71E-07 0.000 mg/dscm 3.10E-04 3.13E-04 3.01E-04 0.000 mg/dscm@7%O2 3.22E-04 3.30E-04 3.15E-04 0.000


### Compound: Nickel Average RunNumber 1 2 3 Mass_mg 0.9466 1.04529 0.84329 0.945 Elb/hr 7.67E-01 8.40E-01 7.04E-01 0.770 lb/mmBtuO2 2.24E-04 2.56E-04 2.16E-04 0.000 mg/dscm 2.50E-01 2.82E-01 2.39E-01 0.257 mg/dscm@7%O2 2.59E-01 2.97E-01 2.50E-01 0.269


### Compound: Phosphorus (yellow or white) Average RunNumber 1 2 3 Mass_mg 0.26807 0.07408 0.26804 0.203 Elb/hr 2.17E-01 5.95E-02 2.24E-01 0.167 lb/mmBtuO2 6.34E-05 1.81E-05 6.85E-05 0.000 mg/dscm 7.09E-02 2.00E-02 7.60E-02 0.056 mg/dscm@7%O2 7.35E-02 2.11E-02 7.94E-02 0.058


### Compound: Selenium Average RunNumber 1 2 3 Mass_mg 0.0067 0.0047 0.0053 0.006 Elb/hr 5.43E-03 3.78E-03 4.42E-03 0.005 lb/mmBtuO2 1.59E-06 1.15E-06 1.35E-06 0.000 mg/dscm 1.77E-03 1.27E-03 1.50E-03 0.002 mg/dscm@7%O2 1.84E-03 1.34E-03 1.57E-03 0.002



### Location: Stack Exit - Method 6C



### Friday, February 11, 2011 Page 18 of 33

### Compound: Sulfur Dioxide Average Run 1 2 3 Elb/hr 3.22E+03 3.37E+03 3.55E+03 3,380.000 lb/mmBtuO2 9.50E-01 1.03E+00 1.06E+00 1.013 ppm 3.93E+02 4.24E+02 4.41E+02 419.333 ppm@7%O2 4.13E+02 4.47E+02 4.63E+02 441.000



### Location: Stack Exit - Method 7E 

### Compound: Nitrogen oxides (NOx) Average Run 1 2 3 Elb/hr 1.19E+03 1.19E+03 1.23E+03 1,203.333 lb/mmBtuO2 3.53E-01 3.62E-01 3.69E-01 0.361 ppm 2.03E+02 2.08E+02 2.13E+02 208.000 ppm@7%O2 2.13E+02 2.19E+02 2.24E+02 218.667



### Location: Stack Exit - OTM - 27/28 

### Compound: Filterable Particulate Average RunNumber 1 2 3 Mass_mg 85 93.2 195.6 124.600 Elb/hr 7.12E+01 8.94E+01 1.67E+02 109.200 gr/dscf 1.01E-02 1.31E-02 2.34E-02 0.016 gr/dscf@7%O2 1.06E-02 1.37E-02 2.46E-02 0.016 lb/mmBtuO2 2.09E-02 2.70E-02 4.86E-02 0.032


### Compound: Filterable PM2.5 Average RunNumber 1 2 3 Mass_mg 83.6 88.3 194.5 122.133 Elb/hr 7.00E+01 8.47E+01 1.66E+02 106.900 gr/dscf 9.91E-03 1.24E-02 2.33E-02 0.015 gr/dscf@7%O2 1.04E-02 1.30E-02 2.45E-02 0.016 lb/mmBtuO2 2.06E-02 2.56E-02 4.84E-02 0.032


### Compound: Inorganic (Aqueous) Condensible Pa Average RunNumber 1 2 3 Mass_mg 48.3 32.8 24 35.033 Elb/hr 4.04E+01 3.15E+01 2.05E+01 30.800 gr/dscf 5.72E-03 4.61E-03 2.87E-03 0.004 gr/dscf@7%O2 6.02E-03 4.82E-03 3.02E-03 0.005 lb/mmBtuO2 1.19E-02 9.52E-03 5.97E-03 0.009


### Compound: Organic Condensible Particulate Average RunNumber 1 2 3 Mass_mg 4.3 14.4 16.3 11.667 Elb/hr 3.60E+00 1.38E+01 1.39E+01 10.433 gr/dscf 5.10E-04 2.03E-03 1.95E-03 0.001 gr/dscf@7%O2 5.37E-04 2.12E-03 2.05E-03 0.002



### Friday, February 11, 2011 Page 19 of 33

### Process Run Data lb/mmBtuO2 1.06E-03 4.18E-03 4.05E-03 0.003


### Compound: Total Particulate Average RunNumber 1 2 3 Mass_mg 135.6 138.4 233.9 169.300 Elb/hr 1.14E+02 1.33E+02 2.00E+02 149.000 gr/dscf 1.61E-02 1.95E-02 2.80E-02 0.021 gr/dscf@7%O2 1.70E-02 2.04E-02 2.95E-02 0.022 lb/mmBtuO2 3.34E-02 4.02E-02 5.82E-02 0.044


### Compound: Total PM2.5 Average RunNumber 1 2 3 Mass_mg 134.2 133.5 232.8 166.833 Elb/hr 1.12E+02 1.28E+02 1.99E+02 146.333 gr/dscf 1.59E-02 1.88E-02 2.78E-02 0.021 gr/dscf@7%O2 1.67E-02 1.96E-02 2.93E-02 0.022 lb/mmBtuO2 3.31E-02 3.87E-02 5.79E-02 0.043



### Friday, February 11, 2011 Page 20 of 33

### Process Run Data



### Run Name Value UOM Comments Target Value 1 Average Heat Input 2901 MMBtu/hr RUN 1 0


### 2 Average Heat Input 0 MMBtu/hr 0
3 Average Heat Input 0 MMBtu/hr 0
1 Fuel Oil Firing Rate 18664 gal/hr RUN 1 0


### 2 Fuel Oil Firing Rate 0 gal/hr 0
3 Fuel Oil Firing Rate 0 gal/hr 0
1 Flue Gas Flow Rate 814009 RUN 1 0


### 1 Flue Gas Oxygen Content 7.78 % RUN 1 0
1 Flue Gas Carbon Dioxide Content 10.57 % RUN 1 0
1 Flue Gas Moisture Content 10.12 % RUN 1 0


### 1 Flue Gas Sampling Point Temperature 220 Deg F RUN 1 0
1 Flue Gas Pressure 29.55 "Hg RUN 1 0
1 Standard Pressure 29.92 "Hg RUN 1 0


### 1 Standard Temperature 68 Deg F RUN 1 0
1 Unit Gross Electrical Output 312 Mwe RUN 1 0
1 Unit Net Electric Generation 287 MWh RUN 1 0


### 4 Average Heat Input 2910 MMBtu/hr RUN 2 0
4 Fuel Oil Firing Rate 18693 gal/hr RUN 2 0
4 Flue Gas Flow Rate 797236 RUN 2 0


### 4 Flue Gas Oxygen Content 7.7 % RUN 2 0
4 Flue Gas Carbon Dioxide Content 10.46 % RUN 2 0
4 Flue Gas Moisture Content 10.21 % RUN 2 0


### 4 Flue Gas Sampling Point Temperature 221 Deg F RUN 2 0
4 Flue Gas Pressure 29.58 "Hg RUN 2 0


### 4 Standard Pressure 29.92 "Hg RUN 2 0
4 Standard Temperature 68 Deg F RUN 2 0
4 Unit Gross Electrical Output 287 Mwe RUN 2 0


### 4 Unit Net Electric Generation 312 MWh RUN 2 0
5 Average Heat Input 2915 MMBtu/hr RUN 3 0
5 Fuel Oil Firing Rate 18702 gal/hr RUN 3 0


### 5 Flue Gas Flow Rate 802626 RUN 3 0
5 Flue Gas Oxygen Content 7.65 % RUN 3 0
5 Flue Gas Carbon Dioxide Content 10.45 % RUN 3 0



### Friday, February 11, 2011 Page 21 of 33

### APCD Run Data

Process Lab Run Data 5 Flue Gas Moisture Content 10.61 % RUN 3 0


### 5 Flue Gas Sampling Point Temperature 224 Deg F RUN 3 0
5 Flue Gas Pressure 29.59 "Hg RUN 3 0
5 Standard Pressure 29.92 "Hg RUN 3 0


### 5 Standard Temperature 68 Deg F RUN 3 0
5 Unit Gross Electrical Output 312 Mwe RUN 3 0
5 Unit Net Electric Generation 287 MWh RUN 3 0

Run Name Value UOM Comments 

### 1 Fuel Higher Heating Value 17700 Btu/lb 1 Fuel Moisture 0.070 % 1 Fuel Mercury Content 0.031 ppm 

### 1 Fuel Cadmium Content 0.49 ppm 1 Fuel Nickel Content 4.5 ppm 1 Fuel Arsenic Content 2 ppm 1 Fuel Chromium Content 1.5 ppm 

### 1 Fuel Beryllium Content 0.98 ppm 1 Fuel Lead Content 1.5 ppm 1 Fuel Manganese Content 1.5 ppm 

### 1 Fuel Chlorine Content 61.6 ppm 1 Fuel Fluorine Content 150 ppm 1 Fuel Cobalt Content 0.28 ppm 1 Fuel Antimony Content 5.9 ppm 

### 1 Fuel Phospohorous Content 5.6 ppm 1 Fuel Selenium Content 0.91 ppm 2 Fuel Higher Heating Value 17800 Btu/lb 

### 2 Fuel Moisture 0.091 % 2 Fuel Mercury Content 0.032 ppm 2 Fuel Cadmium Content 0.47 ppm 2 Fuel Nickel Content 4.4 ppm 

### 2 Fuel Arsenic Content 1.9 ppm 2 Fuel Chromium Content 1.4 ppm 2 Fuel Beryllium Content 0.94 ppm 

### 2 Fuel Lead Content 1.4 ppm 2 Fuel Manganese Content 0.2 ppm 2 Fuel Chlorine Content 62.7 ppm 2 Fuel Fluorine Content 150 ppm



### Friday, February 11, 2011 Page 22 of 33

### 2 Fuel Cobalt Content 0.3 ppm



### 2 Fuel Antimony Content 5.6 ppm 2 Fuel Phospohorous Content 4.8 ppm 2 Fuel Selenium Content 0.78 ppm 3 Fuel Higher Heating Value 17700 Btu/lb 

### 3 Fuel Moisture 0.071 % 3 Fuel Mercury Content 0.031 ppm 3 Fuel Cadmium Content 0.42 ppm 

### 3 Fuel Nickel Content 4.1 ppm 3 Fuel Arsenic Content 1.7 ppm 3 Fuel Chromium Content 1.3 ppm 3 Fuel Beryllium Content 0.85 ppm 

### 3 Fuel Lead Content 1.3 ppm 3 Fuel Manganese Content 1.3 ppm 3 Fuel Chlorine Content 110 ppm 

### 3 Fuel Fluorine Content 150 ppm 3 Fuel Cobalt Content 0.26 ppm 3 Fuel Antimony Content 5.1 ppm 3 Fuel Phospohorous Content 4.8 ppm 

### 3 Fuel Selenium Content 0.67 ppm 4 Fuel Higher Heating Value 17600 Btu/lb 4 Fuel Moisture 0.089 % 

### 4 Fuel Mercury Content 0.031 ppm 4 Fuel Cadmium Content 0.49 ppm 4 Fuel Nickel Content 6.3 ppm 4 Fuel Arsenic Content 2 ppm 

### 4 Fuel Chromium Content 1.5 ppm 4 Fuel Beryllium Content 0.98 ppm 4 Fuel Lead Content 1.5 ppm 

### 4 Fuel Manganese Content 1.5 ppm 4 Fuel Chlorine Content 114 ppm 4 Fuel Fluorine Content 150 ppm 4 Fuel Cobalt Content 0.32 ppm 

### 4 Fuel Antimony Content 5.9 ppm 4 Fuel Phospohorous Content 4.8 ppm 4 Fuel Selenium Content 0.82 ppm 

### 5 Fuel Higher Heating Value 17600 Btu/lb 5 Fuel Moisture 0.045 % 5 Fuel Mercury Content 0.031 ppm 5 Fuel Cadmium Content 0.46 ppm 

### 5 Fuel Nickel Content 3.9 ppm 5 Fuel Arsenic Content 1.8 ppm 5 Fuel Chromium Content 1.4 ppm



### Friday, February 11, 2011 Page 23 of 33

### 5 Fuel Beryllium Content 0.91 ppm



### 5 Fuel Lead Content 1.4 ppm 5 Fuel Manganese Content 1.4 ppm 5 Fuel Chlorine Content 110 ppm 5 Fuel Fluorine Content 150 ppm 

### 5 Fuel Cobalt Content 0.26 ppm 5 Fuel Antimony Content 5.5 ppm 5 Fuel Phospohorous Content 4.8 ppm 

### 5 Fuel Selenium Content 0.7 ppm 6 Fuel Higher Heating Value 17600 Btu/lb 6 Fuel Moisture 0.057 % 6 Fuel Mercury Content 0.033 ppm 

### 6 Fuel Cadmium Content 0.44 ppm 6 Fuel Nickel Content 3.9 ppm 6 Fuel Arsenic Content 1.8 ppm 

### 6 Fuel Chromium Content 1.3 ppm 6 Fuel Beryllium Content 0.88 ppm 6 Fuel Lead Content 1.3 ppm 6 Fuel Manganese Content 1.3 ppm 

### 6 Fuel Chlorine Content 239 ppm 6 Fuel Fluorine Content 150 ppm 6 Fuel Cobalt Content 0.29 ppm 

### 6 Fuel Antimony Content 5.3 ppm 6 Fuel Phospohorous Content 4.8 ppm 6 Fuel Selenium Content 0.69 ppm



### Friday, February 11, 2011 Page 24 of 33

### Sampling / Stack Data Results Detail



### Location Stack Exit - Method 10 Average Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 11, 2011 Page 25 of 33

### Location Stack Exit - Method 23 Average

Run Number 1 2 3 Test Date 5/11/2010 5/12/2010 5/12/2010 Run Start Time 2:12:00 PM 7:25:00 AM 2:35:00 AM Run Finish Time 11:50:00 PM 3:34:00 PM 1/1/1900 2:15:00 AM Net Traversing Points 50 49 49 Net Run Time, minutes 480 480 480 Nozzle Diameter, inches 0.206 0.206 0.206 0.206 Pitot Tube Coefficient 0.81 0.825 0.82 0.818 Dry Gas Meter Calibration Factor 0.985 0.989 0.989 0.988 Barometric Pressure, inches of Mercury 29.66 29.71 29.7 29.690 Average Orifice Meter Differential, inches H2O 1.52 1.54 1.32 1.460 Dry Gas Meter Volume Sampled, cubic feet 335.693 345.152 319.260 333.368 Average Dry Gas Meter Temperature, °F 90.82 96.61 97.23 94.887 Dry Gas Meter Volume Sampled, dscf 315.388 322.762 297.956 312.035 Total Moisture Liquid collected, g 668.6 753 713 711.533 Volume of Water Vapor, standard cubic feet 31.47 35.44 33.56 33.490 Moisture Content of Stack Gas, % 9.07 9.89 10.12 9.693 Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000 Dry Mole Fraction 0.9093 0.9011 0.8988 0.903 Carbon Dioxide, % 10.5 10.4 10.5 10.467 Oxygen, % 7.7 7.6 7.7 7.667 Carbon Monoxide & Nitrogen, % 81.8 82 81.8 81.867 Fuel Factor 1.26 1.28 1.26 Dry Molecular Weight, lb/lb-Mole 29.99 29.97 29.99 29.983 Wet Molecular weight, lb/lb-Mole 28.90 28.79 28.78 28.823 Flue Gas Static Pressure, inches of H2O -1.5 -1.4 -1.4 -1.433 Absolute Flue Gas Pressure, inches of Mercury 29.55 29.61 29.60 29.587 Average Stack Gas Temperature, °F 219.63 232.44 225.94 226.003 Average Velocity Head, inches of H2O 1.2273352792 3844 1.170103255

7261 1.119803964

52806 1.172

Average Stack Gas Velocity, feet/second 68.44 68.76 66.57 67.923 Stack Cross-Sectional Area, square feet 283.529 283.529 283.529 283.529 Dry Volumetric Flow Rate, dry scfm 812,312.6 795,401.1 775,118.8 794,277.500 Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,164,283.5 1,169,727.2 1,132,471.5 1,155,494.0 67 Percent Isokinetic of Sampling Rate, % 99.1 103.6 98.1 100.267 Percent Excess Air, % 55.4 54.1 55.4 54.967 F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000 Round Duct Diameter, inches 228 228 228 Rectangular Duct Width, inches 0 0 0 Rectangular Duct Length, inches 0 0 0 Fw 10320 10320 10320 10,320.000 Fc 1420 1420 1420 1,420.000



### Friday, February 11, 2011 Page 26 of 33

### Location Stack Exit - Method 25A Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 11, 2011 Page 27 of 33

### Location Stack Exit - Method 29 Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, February 11, 2011 Page 28 of 33

### Location Stack Exit - Method 3A CO2 Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 11, 2011 Page 29 of 33

### Location Stack Exit - Method 3A O2 Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 11, 2011 Page 30 of 33

### Location Stack Exit - Method 6C Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 11, 2011 Page 31 of 33

### Location Stack Exit - Method 7E Average

Run Number Test Date Run Start Time Run Finish Time Carbon Dioxide, % Oxygen, % Fuel Factor Dry Volumetric Flow Rate, dry scfm F-Factor, dscfm/MMBtu @ %O2 Moisture, % Analyzer Make Analyzer Model Analyzer Serial Number Operating Range Operating Units No. Readings/Avg. Calibration Set Calibration Pre Zero Cylinder ID Calibration Pre Zero Cylinder Instrument Response Calibration Pre Zero Cylinder Bias Calibration Pre Zero Cylinder Drift Calibration Pre High Cylinder ID Calibration Pre High Cylinder Instrument Response Calibration Pre High Cylinder Bias Calibration Pre High Cylinder Drift Calibration Post Zero Cylinder ID Calibration Post Zero Cylinder Instrument Response Calibration Post Zero Cylinder Bias Calibration Post Zero Cylinder Drift Calibration Post High Cylinder ID Calibration Post High Cylinder Instrument Response Calibration Post High Cylinder Bias Calibration Post High Cylinder Drift Cavg Cavg Units Cgas Cgas Units Fuel Type Fw Fc Cgasw Cgasw Units



### Friday, February 11, 2011 Page 32 of 33

### Location Stack Exit - OTM - 27/28 Average

Run Number Test Date Run Start Time Run Finish Time Net Traversing Points Net Run Time, minutes Nozzle Diameter, inches Pitot Tube Coefficient Dry Gas Meter Calibration Factor Barometric Pressure, inches of Mercury Average Orifice Meter Differential, inches H2O Dry Gas Meter Volume Sampled, cubic feet Average Dry Gas Meter Temperature, °F Dry Gas Meter Volume Sampled, dscf Total Moisture Liquid collected, g Volume of Water Vapor, standard cubic feet Moisture Content of Stack Gas, % Moisture Saturation at Stack Gas Temperature, % Dry Mole Fraction Carbon Dioxide, % Oxygen, % Carbon Monoxide & Nitrogen, % Fuel Factor Dry Molecular Weight, lb/lb-Mole Wet Molecular weight, lb/lb-Mole Flue Gas Static Pressure, inches of H2O Absolute Flue Gas Pressure, inches of Mercury Average Stack Gas Temperature, °F Average Velocity Head, inches of H2O Average Stack Gas Velocity, feet/second Stack Cross-Sectional Area, square feet Dry Volumetric Flow Rate, dry scfm Actual Wet Volumetric Flue Gas Flow Rate, acfm Percent Isokinetic of Sampling Rate, % Percent Excess Air, % F-Factor, dscfm/MMBtu @ %O2 Round Duct Diameter, inches Rectangular Duct Width, inches Rectangular Duct Length, inches Fw Fc



### Friday, February 11, 2011 Page 33 of 33