Title Page 

Facilitv ID· 

Revision#: 

800074 

54 

South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Date· January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

6801 2ND ST 

LONG BEACH, CA 90803 

NOTICE 

IN ACCORDANCE WITH RULE 206, THIS PERMIT TO OPERA TE OR A COPY THEREOF 

MUST BE KEPT AT THE LOCA TlON FOR WHICH IT IS ISSUED. 

THIS PERMIT DOES NOT AUTHORIZE THE EMISSION OF AIR CONTAMINANTS IN EXCESS 

OF THOSE ALLOWED BY DIVISION 26 OF THE HEAL TH AND SAFETY CODE OF THE 

STATE OF CALIFORNIA OR THE RULES OF THE SOUTH COAST AIR QUALITY 

MANAGEMENT DISTRICT. THIS PERMIT SHALL NOT BE CONSTRUED AS PERMISSION TO 

VIOLATE EXISTING LAWS, ORDINANCES, REGULATIONS OR STATUTES OF ANY OTHER 

FEDERAL, STATE OR LOCAL GOVERNMENTAL AGENCIES. 

Barry R. Wallerstein, D. Env. 

""Tome~ 

Mohsen 

By~&rf- Nazemi, P.E. 

Deputy Executive Officer 

Engineering & Compliance 
Section 

A 

B 

c 

D 

E 

F 

G 

H 

I 

1 

K 

Appendix 

A 

B 

South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Table of Content 

Facilitv ID: 800074 

Revision#: 54 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

TABLE OF CONTENTS 

Description 

Facility Information 

RECLAIM Annual Emission Allocation 

Facility Plot Plan 

Facility Description and Equipment 

Specific Conditions 

Administrative Conditions 

RECLAIM Monitoring and Source Testing 

Requirements 

Recordkeeping and Reporting 

Requirements for RECLAIM Sources 

Permit To Construct and Temporary 

Permit to Operate 

Compliance Plans & Schedules 

Air Toxics 

Title V Administration 

NOx and SOx Emitting Equipment Exempt 

From Written Permit Pursuant to Rule 

219 

Rule Emission Limits 

Revision# Date Issued 

15 01/14/2015 

25 01/14/2015 

TO BE DEVELOPED 

28 01/14/2015 

16 01/14/2015 

12 01/14/2015 

13 01/14/2015 

30 01/14/2015 

JO 01/14/2015 

7 01/14/2015 

8 01/14/2015 

9 01/14/2015 

7 01/14/2015 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

Section A Page: I 

Facilitv ID· 800074 

Revision#: 15 

Date: January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION A: FACILITY INFORMATION 

LEGAL OWNER &/OR OPERA TOR: 

LEGAL OPERATOR (if different than owner): 

EQUIPMENT LOCATION: 

MAILING ADDRESS: 

RESPONSIBLE OFFICIAL: 

TITLE: 

TELEPHONE NUMBER: 

CONTACT PERSON: 

TITLE: 

TELEPHONE NUMBER: 

TITLE V PERMIT ISSUED: 

TITLE V PERMIT EXPIRATION DATE: 

TITLE V 

YES 

LA CITY, DWP HA YNES GENERA TING 

STATION 

680I 2ND ST 

LONG BEACH, CA 90803-4324 

P.O. BOX 51I11 RM# I050 

LOS ANGELES, CA 9005I-5700 

RANDY S. HOWARD 

SENIOR ASSISTANT GENERAL MANAGER 

(2I3) 367-038I 

MARK J. SEDLACEK 

DIRECTOR OF ENVIRONMENTAL SERVICES 

(213) 367-0403 

January I4, 2015 

January I 3, 2020 

RECLAIM 

NOx: 

SOx: 

CYCLE: 

ZONE: 

YES 

NO 

l 

COASTAL 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4 I 78 

FACILITY PERMIT TO OPERATE 

Section B Page: I 

Facilitv ID: 800074 

Revision # · 25 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION B: RECLAIM ANNUAL EMISSION ALLOCATION 

The annual allocation of NOx RECLAIM Trading Credits (RTCs) for this facility is calculated 

pursuant to Rule 2002. Total NOx emission shall not exceed such annual allocations unless the 

operator obtains RTCs corresponding to the facility's increased emissions in compliance with 

Rules 2005 and 2007. 

The level of Starting Allocation plus Non-Tradable Credits used to determine compliance with 

Rule 2005(c)(4) and applicability of Rule 2005(e) - Trading Zone Restrictions is listed on the last 

page of this Section. 

The following table lists the annual allocations that were issued to this facility and the amounts of 

RTCs held by this facility on the day of printing this Section. 

RECLAIM POLLUTANT ANNUAL ALLOCATION (POUNDS) 

NOxRTC NOxRTC l Non-Tradable 2 

Year 

Begin Initially Holding as of Non-Usable End Zone 

(month/year) Allocated 01114/2015 RTCs 

(pounds) (pounds) 

112013 12/2013 Coastal 489016 186880 0 

112014 12/2014 Coastal 489016 378987 0 

112015 12/2015 Coastal 489016 378987 0 

112016 12/2016 Coastal 489016 378987 0 

112017 12/2017 Coastal 489016 378987 0 

112018 12/2018 Coastal 489016 378987 0 

112019 12/2019 Coastal 489016 378987 0 

112020 12/2020 Coastal 489016 378987 0 

1/2021 12/2021 Coastal 489016 378987 0 

112022 12/2022 Coastal 489016 378987 0 

112023 12/2023 Coastal 489016 378987 0 

112024 12/2024 Coastal 489016 378987 0 

!/2025 12/2025 Coastal 489016 378987 0 

1/2026 12/2026 Coastal 489016 378987 0 

!/2027 12/2027 Coastal 489016 378987 0 

1/2028 12/2028 Coastal 489016 378987 0 

!/2029 12/2029 Coastal 489016 378987 0 

Footnotes: 

I. This number may change due to pending trades. emissions reported under Quarterly Certification 

of Emissions Report (QCER) and Annual Pennit Emission Program (APEP) Report required 

pursuant to Rule 2004. or deductions made pursuant to Rule 2010(b). The most recent total RTC 

information can be obtained from the District's RTC Listing. 

2. The use of such credits is subject to restrictions set forth in paragraph (t)(l) of Rule 2002. 
I~ 

South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Section B Page· 2 

Facilitv ID: 800074 

Revision #: 25 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION B: RECLAIM ANNUAL EMISSION ALLOCATION 

The annual allocation of NOx RECLAIM Trading Credits (RTCs) for this facility is calculated 

pursuant to Rule 2002. Total NOx emission shall not exceed such annual allocations unless the 

operator obtains RTCs corresponding to the facility's increased emissions in compliance with 

Rules 2005 and 2007. 

The level of Starting Allocation plus Non-Tradable Credits used to determine compliance with 

Rule 2005(c)(4) and applicability of Rule 2005(e) - Trading Zone Restrictions is listed on the last 

page of this Section. 

The following table lists the annual allocations that were issued to this facility and the amounts of 

RTCs held by this facility on the day of printing this Section. 

RECLAIM POLLUTANT ANNUAL ALLOCATION (POUNDS) 

NOxRTC NOxRTC I Non-Tradable 

Year Initially Holding as of Non-Usable Begin End Zone 

(month/year) Allocated 01/14/2015 RTCs 

(pounds) (pounds) 

1/2030 12/2030 Coastal 489016 378987 0 

Footnotes: 

I. This number may change due to pending trades, em1ss1ons reported under Quarterly Certification 

of Emissions Report (QCER) and Annual Permit Emission Program (APEP) Report required 

pursuant to Rule 2004, or deductions made pursuant to Rule 2010(b). The most recent total RTC 

information can be obtained from the District's RTC Listing. 

2. The use of such credits is subject to restrictions set forth in paragraph (t)( 1) of Rule 2002. 

2 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-4178 

FACILITY PERMIT TO OPERATE 

Section B Page· 3 

Facility JD 800074 

Revision#: 25 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION B: RECLAIM ANNUAL EMISSION ALLOCATION 

The annual allocation of RECLAIM Trading Credits (RTCs) for this facility 1s 

calculated pursuant to Rule 2002. If the facility submits a permit application to 

increase in an annual allocation to a level greater than the facility's starting 

Allocation plus Non-Tradable credits as listed below, the application will be 

evaluated for compliance with Rule 2005 (c)(4). Rule 2005 (e) - Trading Zone 

Restrictions applies if an annual allocation is increased to a level greater than the 

facility's Starting Allocation plus Non-Tradable Credits: 

Year NOx RTC Non-Tradable 

Begin End Zone Starting Allocation Credits(NTC) 

(month/year) (pounds) (pounds) 

1/1994 12/1994 Coastal 3666443 0 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

FACILITY PERMIT TO OPERATE 

Section C Page: I 

Facility ID: 800074 

Revision#: 8 

Date· January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION C: FACILITY PLOT PLAN 

(TO BE DEVELOPED) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: I 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14.2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

System. I: BQ1LERS 

BOILER, UNIT NO. I, FUEL OIL, 

NATURAL GAS, COMBUSTION 

ENGINEERING, FRONT FIRED. AIR 

PREHEATED, WITH OXYGEN 

CONTENT CONTROL, 2240 

MMBTU/HR WITH 

A/N: 410730 

GENERATOR, 230 MW 

INJECTOR, MAGNESIUM 

COMPOUNDS, FUEL OIL 

ADDITIVE SYSTEM 

SELECTIVE CATALYTIC 

REDUCTION, NO. I, TWO BABCOCK 

& WILCOX REACTORS, WITH 72 

FULL MODULES AND 6 HALF 

MODULES, CATALYST VOLUME 

3850 CU. FT., WIDTH: 19 FT 3 !N; 

HEIGHT: 23 FT 9 IN; LENGTH: 9 FT 

IOINWITH 

AIN: 541988 

AMMONIA INJECTION, UNIT 

NO. I, TWO AMMONIA/AIR 

INJECTION GRIDS, EACH 

HAVING 1104 INJECTION 

NOZZLES 

ID Connected 

No. To 

DI C73 S96 

C73 DI 

C74 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

NOX: MAJOR 

SOURCE** 

Emissions• 

And Requirements 

CO: 2000 PPMV (5) [RULE 4070 

4-2-1982]; i'iOX: 5 PPMV (5A) 

(RULE 2009, 5·11-2001]; NQX: 

12.37 LBS/IOOOGAL FUEL OIL 

(I) [RULE 2012. S-6-2005); PM: 

0.1 GRA!NS/SCF (5) [RULE 409, 

'8-7-1981]; S02: (9) [40CFR 72-

Acid Rain Provisions, 

11-24-1997); SOX: 500 PPMV 

FUEL OIL (5) [RllLE 407, 

4-2-1982) 

NH3: 10 PPMV FUEL OIL (4) 

[RULE 1303(a)(l)-BACT, 

S-10-1996; RULE 1303(a)(/) 

-BACT, 12-6-2002); NH3: 20 

PPMV NATURAL GAS (4) 

(RULE IJOJ(a)(l)-BACT, 

5-10-1996; RULE /303(a)(/J 

-BACT. 12-6-2002] 

• (I) (IA} ( 18) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (5A) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

Conditions 

Al95.5, 

B59.!, 

DI82.I, 

D371.l, 

E202.l, 

E204.I, 

E204.2, 

Kl71.l 

A99.I, Dl2.2, 

Dl2.3, D28.3, 

0298, E73.I, 

El79.l, 

El79.2 

(7) Denotes NSR applicability limit (8) (SA) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits (10) See section J forNESHAP/MACT requirements 

** Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 2 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

STACK. BOILER NO. I S96 DI 

A/N: 410730 

BOILER. UNIT NO. 2, FUEL OIL, D4 C75 S97 NOX: MAJOR CO: 2000 PPMV (5) [RULE 407, Al95.5, 

NATURAL GAS. COMBUSTION SOURCE** 4-2-1982); NOX: 5 PPMV (SA) B59.l, 

ENGINEERING. FRONT FIRING, AIR [RULE 2009, 5-11-2001); NOX: 0182.l. 

PREHEATED, WITH OXYGEN 12.37 LBS/IOOO GAL FUEL OIL 0371.l, 

CONTENT CONTROL, 2240 (I) [RULE 2012, 5-6-2005); PM: E202. l, 

MMBTU/HR WITH O. l GRAINS/SCF (5) [RULE 409, E204. l, 

A/N: 410732 8-7-1981); S02: (9) [40CFR 72 - E204.2. 

Add Rain Provisions, Kl71.l 

11-24-1997): SOX: 500 PPMV 

FUEL OIL (5) [RULE 407, 

4-2-1982) 

INJECTOR, MAGNESIUM 

COMPOUNDS. FUEL OIL 

ADDlTlVE SYSTEM 

GENERATOR, 230 MW 

SELECTIVE CATALYTIC C75 D4 NH3: lO PPMV FUEL OIL (4) A99. l, 012.2, 

REDUCTION. NO. 2, TWO BABCOCK [RULE 1303(a)(l)-BACT, Dl2.3, 02S.3, 

& WILCOX REACTORS, WITH 72 5-10-1996; RULE /303(a)(/) 029.S, E73.l, 

FULL MODULES AND 6 HALF -BACT, 12-6-2002); NH3: 20 E179.1, 

MODULES. CATALYST VOLUME PPMV NATURAL GAS (4) El79.2 

3S50 CU. FT .• WIDTH: 19 FT 3 IN; [RULE 1303(a)(l)-BACT, 

HEIGHT: 23 FT 9 IN; LENGTH: 9 FT 5-10-1996; RULE /303(a)(l) 

IO IN WITH -BACT. 12-6-2002) 

A/N: 5419S9 

AMMONIA INJECTION, UNIT C76 

NO. 2, TWO AMMONIA/AIR 

INJECTION GRIDS, EACH 

HAVING 1104 INJECTION 

NOZZLES 

* (1) (IA) (lB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (SA) (SB) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (S) (SA) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS. etc.) 

(9) See App B for Emission Limits (I 0) See section J for NESHAP/MACT requirements 

** Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive. Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page· 3 

Facility ID· 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

• (1) (IA) (IB) Denotes RECLAIM emission factor 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

( 9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions· 

And Requirements 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(IO) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 4 

Facility JD· 800074 

Revision#: 28 

Date· January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

GAS TURBINE, UNIT NO. 9, DIESEL 

FUEL, NATURAL GAS, GENERAL 

ELECTRIC, MODEL PG724IFA, 

COMBINED CYCLE, WATER 

INJECTION (DIESEL FIRING ONLY), 

WITH LOW NOX BURNER, 1757 

MMBTU/HR WITH 

A/N: 517866 

GENERA TOR, (MAX GROSS 

OUTPUT AT 65 DEG. F), 169.9 

MW 

Dl25 

• (1) (lA) (18) Denotes RECLAIM emission factor 

CI30 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

NOX: MAJOR 

SOURCE•• 

Emissions* 

And Requirements 

CO: 4 PPMV (4) [RULE I303(a) 

(1)-BACT, S-10-19%; RULE 

l 303(a)(l)-BACT, 12-6-2002]; 

CO: 2000 PPMV (5) [RULE 407, 

4-2-1982]; NOX: 2 PPMV 

NATURAL GAS (4) [RULE 

2005, S-6-2005]: NOX: 22.16 

LBS/ IOOO GAL DIESEL (I) 

[RULE 2012, S-6-2005]; NOX: 

111 PPMV NATURAL GAS (8) 

[40CFR 60 Subpart GG, 

3-<H981]; NOX: 121 PPMV 

DIESEL (8) [40CFR 60 Subpart 

GG,3-6-1981]; PM: 0.01 

GRAINS/SCF (SA) [RULE 47S, 

10-8-1976; RULE 475, 8-7-1978]; 

PM: 0.1 GRAINS/SCF 

NATURAL GAS (5) [RULE 409, 

8-7-1981]; PM: II LBS/HR (5B) 

[RULE 475, 10-8-1976; RULE 

475. 8-7-1978]; S02: (9) [40CFR 

72 - Acid Rain Provisions, 

11-24-1997]; SOX: 150 PPMV (8) 

[40CFR 60 Subpart GG, 

3-6-1981]; SOX: 500 PPMV 

FUEL OIL (5) [RULE 407, 

4-2-1982]; voe: 2 PPMV (4) 

[RULE 1303(a)(l)-BACT, 

5-10-19%; RULE 1303(a)(l) 

-BACT, 12-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

A63.3, A99.2, 

A99.3, 

Al95. l, 

Al95.2, 

Al95.3, 

A327.l, 

A433.I, 

875.1, D29.4, 

D29.5, D82.l, 

D82.2, 

D372.I,E57.I, 

EI93.l, K40.3, 

K67.4 

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring. recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar. CA 91765-4178 

Section D 

facility ID 

Revision#: 

Page: 5 

800074 

28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

GENERATOR, HEAT RECOVERY 

STEAM 

STEAM TURBINE, STEAM, UNIT 

NO. 8, COMMON TO GAS 

TURBINES NO. 9 AND NO. IO, 257 

MW (AT 65 DEG. F) 

BURNER, DUCT, NATURAL GAS, 

LOCATED IN THE HRSG OF 

TURBINE NO. 9, 286.6 MMBTU/HR 

A/N: 517866 

0129 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

CI30 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (5B) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

NOX:MAJOR 

SOURCE** 

Emissions• 

And Requirements 

CO: 4 PPMV (4) [RULE IJOJ(a) 

(l)-BACT,5-10-1996; RULE 

I 303(a}(l)-BACT. I 2-6-2002]; 

CO: 2000 PPMV (5) [RULE 407, 

4-2-1982]; NOX: 0.2 

LBS/MMBTU NATURAL GAS 

(8) [40CFR 60 Subp8't Da, 

10-4-1991]; NOX: 2 PPMV 

NATURAL GAS (4) [Rlll.E 

2005, 5-6-2005]; PM: O.ot 

GRAINS/SCF (5A) [RULE 475, 

10-8-1976; RULE 475, 8-7-1978]; 

PM: 0.03 LBS/MMBTU 

NATURAL GAS (8) (40CFR 60 

Subpart Da, 10-4-1991 ]; PM: 0.1 

GRAINS/SCF NATURAL GAS 

(5)[RULE 409, 8-7-1981]; PM: 11 

LBS/HR (5B) [RULE 475, 

10-8-1976; RULE 475, 8-7-1978]; 

S02: (9) [40CFR 72 - Acid Rain 

Provisions, 11-24-1997); SOX: 

0.2 LBS/MMBTU NATURAL 

GAS (8) [40CFR 60 Subpart Da, 

10-4-1991]; voe: 2 PPMV (4) 

[RULE IJOJ(a)(l)-BACT, 

5-10-1996; RULE 1303(a}(l) 

-BACT. I 2-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

A63.3,A99.2, 

A99.3, 

Al95.I, 

Al95.2, 

Al95.3, 

A327.I, 

A433.I, 

B75.I, 029.4, 

029.5, 082. I, 

D82.2, 

D372.1,E57.I, 

El93.I, K40.3, 

K67.4 

(8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(I 0) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

Section D Page: 6 

Facility ID: 800074 

Revision#: 28 

Date· January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

CO OXIDATION CATALYST, 

SERVING UNIT NO. 9, HITACHI, 

MITSUBISHI, PEERLESS OR EQUAL, 

HEIGHT:61 FT; LENGTH:26 FT; 

WIDTH:4 FT; WITH 6344 CUBIC 

FEET OF CATALYST VOLUME 

A/N: 432467 

SELECTIVE CATALYTIC 

REDUCTION, SERVING UNIT NO. 9, 

HITACHI, MITSUBISHI, PEERLESS 

OR EQUAL, HEIGHT: 61 FT; 

LENGTH:26 FT; WIDTH: 5 FT, WITH 

7930 CU FEET OF CATALYST 

VOLUME WITH 

A/N: 432467 

AMMONIA INJECTION, 

INJECTION GRID 

STACK, SERVING UNIT NO. 9, 

HEIGHT: 140 FT; DIAMETER: 19 FT 

A/N: 517866 

ID 

No. 

CI30 

Cl31 

SI33 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

Connected 

To 

0125 Dl29 

Cl31 

CI30 SI33 

Cl31 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (5B) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions • 

And Requirements 

NHJ: 5 PPMV NATURAL GAS 

(4) [RULE 1303(a)(l)-BACT, 

5-10-1996; RULE /303(a)(/) 

-BACT, 12-6-2002) 

(2) (2A) (2B) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

Al95.4, 

012.6, 012.7, 

012.8, 029.2, 

E73.2, El 79.3, 

El79.4 

(8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(I 0) See section J for NESHAP/MACT requirements 

• • Refer to section F and G of this permit to detennine the monitoring, recordk.eeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 7 

Facilitv ID: 800074 

Revision#' 28 

Date: January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

GAS TURBINE, UNIT NO IO, DIESEL 

FUEL, NATURAL GAS, GENERAL 

ELECTRIC, MODEL PG724IFA, 

COMBINED CYCLE, WATER 

INJECTION (DIESEL FIRING ONLY), 

wm I LOW NOX BURNER, I 757 

MMBTUIHR WITH 

A/N: 518035 

GENERA TOR, (MAX GROSS 

OUTPUT AT 65 DEG. F), 169.9 

MW 

ID Connected 

No. To 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (SB) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

NOX: MAJOR 

SOURCE** 

Emissions* 

And Requirements 

CO: 4 PPMV (4) [RULE IJOJ(a) 

(l}-BACT, 5-10-1996; RULE 

/303(a)(/)-BACT. I 2-6-2002]; 

CO: 2000 PPMV (5) (RULE 407, 

4-2-1982]; NOX: 2 PPMV 

NATURAL GAS (4) [RULE 

2005, 5-6-2005]: NOX: 22.16 

LBS/IOOO GAL DIESEL (I) 

[RULE 2012,5-6-2005]: NOX: 

I I I PPMV NATURAL GAS (8) 

[40CFR 68 Subpart GG, 

J-6-1981]; NOX: 121 PPMV 

DIESEL (8) [40CFR 60 Subpart 

GG,J-li-1981]: PM: 0.01 

GRAINS/SCF (SA) [RULE 475, 

10-8-1976; RULE 475, 8-7-1978]; 

PM: 0.1 GRAINS/SCF 

NATURAL GAS (5) [RULE 409, 

8-7-1981]: PM: I I LBS/HR (SB) 

[RULE 475, 10-8-1976; RULE 

475, 8-7-1978]: S02: (9) [40CFR 

72 -Acid Rain Provisions. 

11-24-1997]: SOX: 150 PPMV (8) 

[40CFR 60 Subpart GG, 

J-6-1981]: SOX: 500 PPMV 

FUEL OIL (5) [RULE 407, 

4-2-1982]: voe 2 PPMV (4) 

[RULE IJOJ(a)(l}-BACT, 

5-10-1996; RULE 1303(a)(/) 

-BACT, 12-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

A63.2, A99.2, 

A99.3, 

Al95.I, 

Al95.2, 

AI95.3, 

A327.I, 

A433.I, 

B75. I, D29.4, 

029.5, D82.I, 

D82.2. 

0372. I, E57. I, 

El93.I, K40.3, 

K67.4 

(8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

( 10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requiremen.ts for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 8 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

~roe~···roWINEl::t:YCtilfc&t\S'tlRB:tl'@l6EN'···'rl<Wt¥. ••• :. • •h . . •• ..•• • ..•. , • .... . • . ' . F;. .• .~ s tar·····~·· ' ...... ... ~ . 

GENERATOR, HEAT RECOVERY 

STEAM 

STEAM TURBINE, STEAM, UNIT 

NO. 8, COMMON TO GAS 

TURBINES NO. 9 AND NO. IO, 

257 MW (AT 65 DEG. F) 

BURNER, DUCT, NATURAL GAS, Dl42 Cl38 NOX: MAJOR CO: 4 PPMV (4) (RULE 130J(a) A63.2, A99.2, 

LOCATED IN THE HRSG OF SOURCE*• (l)-BACT,5-10-1996; RULE A99.3, 

TURBINE NO. 10, 286.6 MMBTU/HR 1303(a){/)-8ACT, I 2-6-2002]; Al95.I, 

A/N: 518035 CO: 2000 PPMV (5) [RULE 407, Al95.2, 

4-2-1982]; NOX: 0.2 Al95.3, 

LBS/MMBTU NATURAL GAS A327.I, 

(8) (40CFR60 Subpart Da, A433.I, 

10-4-1991]; NOX: 2 PPMV B75.I, D29.4, 

NATURAL GAS (4) [RULE 029.5' D82. I, 

2005, 5-6-2005]; PM: 0.01 D82.2, 

GRAINS/SCF (5A) [RULE 475, D372.l,E57.I, 

10-8-1976; RULE 475, 8-7-1978]; E193.I, K40.3, 

PM: 0.03 LBS/MMBTU K67.4 

NATURAL GAS (8) (40CFR 60 

Subpart Da, 10-4-1991]; PM: 0.1 

GRAINS/SCF NATURAL GAS 

(5)[RULE 409, 8-7-1981]; PM: II 

LBS/HR (5B) (RULE 475, 

10-8-1976; RULE 475, 8-7-1978]; 

S02: (9) (40CFR 72 - Add aa;n 

Provisions, 11-24-1997): SOX: 

0.2 LBS/MMBTU NATURAL 

GAS (8) (40CFR 60 Subpart Da, 

10-4-1991]; voe: 2 PPMV (4) 

(RULE IJOJ(a)(l)-BACT, 

5-10-1996; RULE 1303(a)(/) 

-BACT, 12-6-2002] 

• (I) (IA) (IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes 8ACT emission limit 

(5) (5A) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits (I 0) See section J for NESHAPIMACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D 

Faci1itv ID: 

Revision#: 

Page: 9 

800074 

28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

yfroceSS)~: ·· ·· ~~:cv<:g;GAS~INEGEN~~TJf),j11$YS~: ~· CO OXIDATION CATALYST, Cl38 Dl34 Cl39 

SERVING UNIT NO. 10, HITACHI, Dl42 

MITSUBISHI, PEERLESS OR EQUAL, 

HEIGHT:61 FT: LENGTH:26 FT; 

WIDTH:4 FT: WITH 6344 CUBIC 

FEET OF CATALYST VOLUME 

A/N: 432466 

SELECTIVE CATALYTIC Cl39 Cl38 Sl41 NHJ: 5 PPMV NATURAL GAS Al95.4, 

REDUCTION, SERVING UNIT NO. I 0, (4) IRULE 1303(•)(1)-BACT, Dl2.6, Dl2.7, 

HEIGHT: 61 FT: LENGTH:26 FT: 5-10-1996; RULE J303(a)(I) Dl2.8, D29.2, 

WIDTH: 5 FT, WITH 7930 CU FEET -BACT, I 2-6-2002) E73.2, El79.3, 

OF CATALYST VOLUME WITH E179.4 

A/N·. 432466 

AMMONIA INJECTION, 

INJECTION GRID 

STACK, SERVING UNIT NO. 10, Sl41 Cl39 

HEIGHT: 140 FT; DIAMETER: 19 FT 

A/N: 518035 

'Proc .. 31 StliPLE't'.VCLE ~..\tS '1'1J'Rij1NE1'9WER'~.ENE~1't'ON'~TE~tl•".'. .';'<"'Si; 

• (I) (IA) ( IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (SA) (SB) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits ( 10) See section J for NESHAP!MACT requirements 

•• Refer to section F and G of this pennit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 10 

Facilitv ID 800074 

Revision#: 28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

lff~~ij'J;; SI ·- -'E'd~Lt·•:TV).ijjlm; lt~~~ON'~f:if'.-~ 

GAS TURBINE, UNIT 11, NATURAL 0159 Cl61 NOX: MAJOR CO: 4 PPMV (4) (RULE 1703- A63.4, A99.6, 

GAS, GENERAL ELECTRIC, MODEL SOURCE** PSD Analysis. 10-7-1988}; CO: Al95.8, 

LMSIOOPA, INTERCOOLED, WITH 2000 PPMV (5) (RULE 407. A195.9, 

WATER INJECTION, WITH WATER 4-2-1982]; NOX: 2.5 PPMY (4) A195. IO, 

INJECTION, 906.6 MMBTU/HR (RULE 1703 - PSD Analysis, A327. I, Ci.4, 

WITH I0-7-1988; RULE 2005. Cl.5, 029.7, 

AIN: 559600 5-6-2005]: NOX: 25 PPMV (8) 082.3, 082.4, 

(40CFR 60 Subpart KKKK. E193.6, 

7+2006]: PM: 0.01 E193.7, 

GRAINS/SCF (SA) (RULE 475, El93.10, 

I0-8-1976; RULE 475, 8-7-1978]: K67.6 

PM: 0.1 GRAINS/SCF (5) [RULE 

409,8-7-I981];PM: II LBS/HR 

(SB) [RULE 475, 10-8-1976; 

RULE 475, 8-7-1978]: PMIO: 5.8 

LBS/HR (4) [RULE IJOJ(b)(2) 

-Offset, 5-10-1996; RULE/ 303(b) 

(2)-0jfsel. 12-6-2002]; S02: (9) 

(40CFR 72 - Atid Rain 

Provisions., 11-24-1997]; 502: 

0.9 LBS/MEGAWATT-HOUR 

(8A) [40CFR 60 Subpart KKKK. 

7-6-2006]; voe: 2 PPMV (4) 

(RULE IJOJ(a)(l)-BACT, 

5-10-1996; RULE /303(a)(I) 

-BACT, I 2-6-2002] 

GENERATOR, GROSS AT65 F, 

I02.7MW 

• ( 1) (IA) ( lB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration Jimit (4) Denotes 8ACT emission 1imit 

(5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits (I 0) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page 11 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

:Pro~!Ji· S9LE~1€LE'~T~EPID\IER~~'fl().N[~STE~f;Wt!··· "'''?!''· . CO OXIDATION CATALYST, BASF, Cl61 Dl59Cl62 

SS FOIL WITH ALUMINA 

WASHCOAT, MODEL CAMET, 80 

MODULES, CATALYST TOTAL 

VOLUME: 160 CUBIC FEET 

AIN:495978 

SELECTIVE CATALYTIC Cl62 Cl61 Sl64 NHJ: 5 PPMV (4) [RULE IJOJ(a) Dl2.9, 

REDUCTION, CORMETECH, MODEL: (1)-BACT, 5-10-1996; RULE Dl2.IO, 

CMHT-27, WITH 12 MODULES, 1211 / 303(a)(l)-BACT: 12-6-2002] Dl2.ll, 

CU.FT WITH D29.8, El79.5, 

A/N: 495978 El79.6, 

E193.9 

AMMONIA INJECTION I 

STACK, SERVING UNIT 11, HEIGHT: Sl64 Cl62 

150 FT: DIAMETER: 13 FT 6 IN 

A/N: 559600 

• (I) (IA) ( 18) Denotes RECLAIM emission factor (2) (2A) (2B) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (5A) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B For Emission Limits (10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this pennit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 12 

Facility ID: 800074 

Revision#: 28 

Date· January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

GAS TURBINE, UNIT 12, NATURAL 

GAS, GENERAL ELECTRIC, MODEL 

LMS I OOPA, INTER COOLED, WITH 

WATER INJECTION, WITH WATER 

INJECTION, 906.6 MMBTU/HR 

WITH 

A/N: 559601 

GENERA TOR, GROSS AT 65 F, 

!02.7MW 

Dl65 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

Cl67 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

NOX: MAJOR 

SOURCE** 

Emissions• 

And Requirements 

CO: 4 PPMV NATURAL GAS 

(4) [RULE 1703- PSD Analysis, 

10-7-1988]; CO: 2000 PPMV (5) 

(RULE 407, 4-2-1982]; NOX: 2.5 

PPMVNATURAL GAS (4) 

[RULE 1703 - PSD Analysis, 

10-7-1988; RULE 2005, 

5-6-2005]; NOX: 25 PPMV 

NATURAL GAS (8) (40CFR 60 

Subpart KKKK, 7-6-2006]; PM: 

0.01 GRAINS/SCFNATURAL 

GAS (SA) )RULE 475, 10-8-1976; 

RULE 475, 8-7-1978]; PM: 0.1 

GRAINS/SCF NATURAL GAS 

(5) (RULE 409, 8-7-1981]: PM: 11 

LBS/HR NATURAL GAS (58) 

(RULE 475, 10-8-1976; RULE 

475. 8-7-1978]; PMlO: 5.8 

LBS/HR (4) (RULE 1303(b)(2) 

-Offset, 5-10-1996; RULE l 303(b) 

(2)-0ffset. 12-6-2002]; S02: (9) 

[ 40CFR 72 - Acid Rain 

Provisions, 11-24-1997]; S02: 

0.9 LBS/MEGAWATT-HOUR 

NATURAL GAS (8A) [40CFR 

60 Subpart KKKK, 7-6-2006]; 

voe: 2 PPMV NATURAL GAS 

(4) [RULE 1303(a)(l)-BACT, 

5-10-1996; RULE 1303(a)(l) 

-BACT. 12-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission liinit 

(6) Denotes air toxic control rule limit 

Conditions 

A63.4, A99.6, 

Al95.8, 

Al95.9, 

Al95. IO, 

A327. I, Cl.4, 

Cl.5, 029.7, 

082.3, 082.4, 

E193.6, 

El93.7, 

El93. 10, 

K67.6 

(8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

( 10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 13 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

CO OXIDATION CATALYST, BASF, 

SS FOIL WITH ALUMINA 

WASHCOAT, MODEL CAMET, 80 

MODULES, CATALYST TOTAL 

VOLUME: 160 CUBIC FEET 

A/N: 495980 

SELECTIVE CATALYTIC 

REDUCTION, CORMETECH, MODEL: 

CMHT-27, WITH I2 MODULES, I2I I 

CU.FT. WITH 

AIN:495980 

AMMONIA INJECTION 

STACK, SERVING UNIT I2, HEIGHT: 

150 FT; DIAMETER: I3FT 6 lN 

AIN: 55960I 

ID 

No. 

C167 

C168 

SI70 

(I) (IA) (18) Denotes RECLAIM emission factor 

Connected 

To 

Dl65 CI68 

CI67 SI70 

CI68 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions • 

And Requirements 

NH3: 5 PPMV (4) [RULE 1303(a) 

(1)-BACT, 5-10-1996; RULE 

/303(a)(/)-BACT, 12-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

DI2.9, 

DI2.IO, 

DI2.II, 

029.8, EI79.5, 

EI79.6, 

EI93.9 

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(10) See section J for NESHAP/MACT requirements 

** Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

Section D Page: 14 

Facilitv lD: 800074 

Revision#: 28 

Date: January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

l''J'~'tL ···s-1)E"Ol~LEG'.\l~'l'~P~~,~~N'•11i:t~lll'' , 'Li;sf<;,: "'" 

GAS TURBINE, UNIT 13, NATURAL Dl71 Cl73 NOX:MAJOR CO: 4 PPMV NATURAL GAS A63.4, A99.6, 

GAS, GENERAL ELECTRIC, MODEL SOURCE** (4)[RULE 1703 - PSD Analysis, Al9S.S, 

LMSIOOPA, INTERCOOLED, WITH 10-7-1988]; CO: 2000 PPMV (S) Al9S.9, 

WATER INJECTION, WITH WATER [RULE 407,4-2-1982]; NOX: 2.S Al9S.l0, 

INJECTION, 906.6 MMBTU/HR PPMV NATURAL GAS ( 4) A327. l, Cl.4, 

WITH [RULE 1703 - PSD Analysis. Cl.5, 029.7, 

A/N: SS9602 10-7-1988; RULE 2005. DS2.3. DS2.4, 

5-6-2005]; NOX: 2S PPMV E193.6, 

NATURAL GAS (S) [40CFR 60 El93.7, 

Subpart KKKK, 7-6-2006]; PM: El93.IO, 

0.01 GRAINSISCF NATURAL K67.6 

GAS (SA) [RULE 475. 10-8-1976; 

RULE 475, 8-7-1978]; PM: 0.1 

GRAINSISCF NATURAL GAS 

(S)(RULE409,8-7-!98l]iPM: II 

LBS/HR NATURAL GAS (SB) 

[RULE 475. 10-8-1976; RULE 

475. 8-7-1978]; PMIO: 5.S 

LBS/HR (4) [RULE IJOJ(b)(2) 

-Offs<t,5-I0-1996; RULE /303(b) 

(2)-0ffset. 11-6-2002); 502: (9) 

[40CFR 72 - Acid Rain 

Provisions.11-24-1997]; S02: 

0.9 LBS/MEGAWATT-HOUR 

NATURAL GAS (SA) [40CFR 

60 Subpart KKKK, 7-6-2006]; 

voe: 2 PPMV NATURAL GAS 

(4) [RULE IJOJ(a)(l)-BACT, 

5-ltH996; RULE /303(a)(I) 

-BACT, 12-6-2002) 

GENERATOR, GROSS AT 6S F, 

102.7MW 

• (I) (IA) (18) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAlM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (S) (SA) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits ( 10) See section J for NESl-lAP/MACT requirements 

•• Refer to section F and G of this pennit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D 

Facilitv ID: 

Revision#: 

Page: 15 

800074 

28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

CO OXIDATION CATALYST, BASF, 

SS FOIL WITH ALUMINA 

WASHCOAT, MODEL CAMET, 80 

MODULES, CATALYST TOTAL 

VOLUME: 160 CUBIC FEET 

AIN: 495988 

SELECTIVE CATALYTIC 

REDUCTION, CORMETECH, MODEL: 

CMHT-27, WITH 12 MODULES, 1211 

CU.FT. WITH 

AIN:495988 

AMMONIA INJECTION 

ST ACK, SERVING UNIT 13, HEIGHT: 

150 FT ; DIAMETER: 13 FT 6 IN 

AIN: 559602 

ID 

No. 

Cl73 

Cl74 

Sl76 

• (1) (IA) (lB) Denotes RECLAIM emission factor 

Connected 

To 

Dl71 Cl74 

Cl73 Sl76 

Cl74 

(3) Denotes RECLAIM concentration limit 

(5) (5A) (5B) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions • 

And Requirements 

NH3: 5 PPMV (4) [RULE 1303(a) 

(1)-BACT, 5-10-1996; RULE 

1303(a)(l)-BACT, 12-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

Dl2.9, 

Dl2.IO, 

Dl2.ll, 

D29.8, E179.5, 

El79.6, 

El93.9 

(8) (SA) (80) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this pennit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page· 16 

Facilitv ID· 800074 

Revision#: 28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

GAS TURBINE, UNIT 14, NATURAL 

GAS, GENERAL ELECTRIC, MODEL 

LMSIOOPA, INTERCOOLED, WITH 

WATER INJECTION, WITH WATER 

INJECTION, 906.6 MMBTU/HR 

WITH 

A/N: 559603 

GENERATOR. GROSS AT 65 F, 

102.7MW 

ID 

No. 

0177 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

Connected 

To 

CI79 

(3) Denotes RECLAIM concentration limit 

(5) (5A) (5B) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

NOX:MAJOR 

SOURCE** 

Emissions* 

And Requirements 

CO: 4 PPMV NATURAL GAS 

(4) [RULE 1703- PSD Analysis, 

10-7-1988]; CO: 2000 PPMV (5) 

[RULE 407, 4-2-1982]; NOX: 2.5 

PPMV NATURAL GAS (4) 

[RULE 1703 - PSD Analysis, 

10-7-1988; RULE 2005, 

5-6-2005]; NOX: 25 PPMV 

NATURAL GAS (8) [40CFR 60 

Subpart KKKK, 7-6-2006]; PM: 

0.01 GRAINS/SCF NATURAL 

GAS (SA) [RULE 475, 10-8-1976; 

RULE 475. 8-7-1978]: PM: 0.1 

GRAINS/SCF NATURAL GAS 

(S)[RULE 409, 8-7-1981]: PM: 11 

LBS/HR NATURAL GAS (SB) 

[RULE 475, 10-8-1976; RULE 

475, 8-7-1978]; PMIO: 5.8 

LBS/HR (4) [RULE 1303(b)(2) 

-Offset,S-10-1996; RULE /303(b) 

(2)-0.ffset. 12-6-2002]: S02: (9) 

[ 40CFR 72 - Acid Rain 

Provisions, 11-24-1997]; S02: 

0.9 LBS/MEGAWATT-HOUR 

NATURAL GAS (8A) [ 40CFR 

60 Subpart KKKK, 7-6-2006]: 

voe: 2 PPMV NATURAL GAS 

(4) [RULE 1303(a)(l)-BACT, 

5-10-1996; RULE /303(a}(1} 

-BACT, 12-6-2002] 

(2) (2A) (2B) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

A63.4, A99.6, 

Al95.8, 

Al95.9, 

Al95.IO, 

A327.l,Cl.4, 

Cl.5, 029. 7, 

082.3, 082.4, 

El93.6, 

El93.7, 

EI93. IO, 

K67.6 

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordk.eeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar. CA 91765-4178 

Section D Page· 1 7 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

CO OXIDATION CATALYST, BASF, 

SS FOIL WITH ALUMINA 

WASHCOAT, MODEL CAMET, 80 

MODULES, CATALYST TOT AL 

VOLUME: 160 CUBIC FEET 

A/N: 495989 

SELECTIVE CATALYTIC 

REDUCTION, CORMETECH, MODEL: 

CMHT-27, WITH 12 MODULES, 1211 

CU.FT. WITH 

A/N: 495989 

AMMONIA INJECTION 

STACK, SERVING UNIT 14, HEIGHT: 

150 FT : DIAMETER: 13 FT 6 IN 

A/N: 559603 

ID 

No. 

Cl79 

Cl80 

Sl82 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

Connected 

To 

Dl77 Cl80 

CI79Sl82 

Cl80 

(3) Denotes RECLAIM concentration limit 

(5) (5A) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions * 

And Requirements 

NHJ: 5 PPMV (4) [RULE 1303(a) 

(1)-BACT, S-J0-1996; RULE 

1303(a)(J)-BACT, 12-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

Dl2.9, 

Dl2.l0, 

012.11, 

029.8, El79.5, 

El79.6, 

E193.9 

(8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(IO) See section J for NESHAP/MACT requirements 

** Refer to section F and G of this pennit to detennine the monitoring, record.keeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 9 t 765-41 78 

Section D 

Facilitv ID: 

Revision#: 

Page: Ti 

800074 

28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

GAS TURBINE, UNIT 15, NATURAL 

GAS, GENERAL ELECTRIC, MODEL 

LMS IOOP A, INTERCOOLED, WITH 

WATER INJECTION, WITH WATER 

INJECTION, 906.6 MMBTU/HR 

WITH 

A/N: 559604 

GENERA TOR, GROSS AT 65 F, 

I02.7MW 

Dl83 

• (I) (IA) (18) Denotes RECLAIM emission factor 

CI85 

(3) Denotes RECLAIM concentration limit 

(5) (5A) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

l 

NOX:MAJOR 

SOURCE** 

Emissions· 

And Requirements 

CO: 4 PPMV NATURAL GAS 

( 4) [RULE 1703 • PSD Analys;s, 

10-7-1988]; CO: 2000 PPMV (5) 

[RULE 407, 4--2-1982]; NOX: 2.5 

PPMVNATURAL GAS (4) 

[RULE 1703 - PSD Analysis, 

10-7-1988; RULE 2005, 

5-6-2005]; NOX: 25 PPMV 

NATURAL GAS (8) [40CFR 60 

Subpart KKKK., 7-6-2006); PM: 

0.01 GRAINS/SCF NATURAL 

GAS (SA) [RULE 475, 10-8-1976; 

RULE 475, 8-7-1978); PM: 0.1 

GRAINS/SCF NATURAL GAS 

(5) [RULE 409, 8-7-1981]; PM: 11 

LBS/HR NATURAL GAS (58) 

[RULE 475, 10-8-1976; RULE 

475, 8-7-1978]; PMIO: 5.8 

LBS/HR (4) [RULE 1303(b)(2) 

-Offset, 5-10-1996; RULE/ 303(b) 

(2)-0ffeet, 12-6-2002]; S02: (9) 

[ 40CFR 72 - Acid Rain 

Provisions, t 1-24-1997]; S02: 

0.9 LBS/MEGAWATT-HOUR 

NATURAL GAS (8A) [40CFR 

60 Subpart KKKK, 7-6-2006]; 

voe: 2 PPMV NATURAL GAS 

(4) [RULE 1303(a)(l)-BACT, 

5-10-1996; RULE /303(a)(l) 

-BACT. 12-6-2002] 

(2) (2A) (2B) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

A63.4, A99.6, 

Al95.8, 

Al95.9, 

AI95. IO, 

A327. I, Cl.4, 

Cl.5, 029.7, 

D82.3, D82.4, 

El93.6, 

El93.7, 

El93.IO, 

K67.6 

(8) (8A) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(I 0) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this pennit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 19 

Facility ID: 800074 

Revision#: 28 

Date· January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions· 

And Requirements 

b7'~SSCT£3=7""'7'7'"'"""2"3'DE3'B'3'8cirr917'l1111E;min,,,,,~"'7""7""7"'1m,_""" 

il~r:~~~j--~-~--•1Mif,•1::. 

CO OXIDATION CATALYST, BASF, 

SS FOIL WITH ALUMINA 

WASHCOAT, MODEL CAMET, 80 

MODULES, CATALYST TOT AL 

VOLUME: 160 CUBIC FEET 

A/N:495990 

SELECTIVE CATALYTIC 

REDUCTION, CORMETECH, MODEL: 

CMHT-27, WITH 12 MODULES, 121 I 

CU.FT WITH 

A/N: 495990 

AMMONIA INJECTION 

STACK, SERVING UNIT I 5, HEIGHT: 

150 FT; DIAMETER: 13 FT 6 IN 

A/N: 559604 

Cl85 

Cl86 

Sl88 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

Dl83 CI86 

Cl85 SI88 

Cl86 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (58) Denotes command and control emission limit 

NHJ: 5 PPMV (4) [RULE 1303(a) 

(1)-BACT, 5-I0-1996; RULE 

/ 303(a)(l)-BACT. 12-6-2002( 

(2) (2A) (2B) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

DI2.9, 

DI2.IO, 

DI2.II, 

D29.8, El79.5, 

EI79.6, 

EI93.9 

(7) 

(9) 

Denotes NSR applicability limit 

See App B for Emission Limits 

(8) (8A) (88) Donotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(I 0) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordk.eeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 20 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

GAS TURBINE, UNIT 16, NATURAL 

GAS, GENERAL ELECTRIC, MODEL 

LMSlOOPA, INTERCOOLED, WITH 

WATER INJECTION, WITH WATER 

INJECTION, 906.6 MMBTUIHR 

WITH 

A/N: SS960S 

GENERA TOR, GROSS AT 6S F, 

102.7MW 

DIS9 

• (1) (IA) (IB) Denotes RECLAIM emission factor 

Cl91 

(3) Denotes RECLAIM concentration limit 

(5) (5A) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

NOX:MAJOR 

SOURCE•• 

Emissions· 

And Requirements 

CO: 4 PPMVNATURAL GAS 

(4) [RULE 1703- PSD Analysis, 

I0-7-19SS]; CO: 2000 PPMV (S) 

[RULE 407, 4-2·1982]; NOX: 2.5 

PPMV NATURAL GAS (4) 

[RULE 1703 - PSD Analysis, 

10-7-1988; RULE 2005, 

5-6-2005]; NOX: 2S PPMV 

NATURAL GAS (S) [40CFR 60 

Subpart KKKK, 7-6-2006]; PM: 

0.01 GRAINS/SCF NATURAL 

GAS (SA) [RULE 475, 10-8-1976; 

RULE 475. 8-7-1978]; PM: 0.1 

GRAINS/SCF NATURAL GAS 

(S)[RULE 409, S-7-1981]; PM: II 

LBS/HR NATURAL GAS (SB) 

[RULE 475, 10-8-1976; RULE 

475, 8-7-1978]; PMJO: 5.S 

LBS/HR (4) [RULE 1303(b)(2) 

-Offset, 5-10-1996; RULE 1303(b) 

(2)-0jfset. 12-6-2002]; S02: (9) 

[40CFR 72 - Acid Rain 

Provisions, 11-24-1997]; S02: 

0.9 LBS/MEGAWATT-HOUR 

NATURAL GAS (SA) [40CFR 

60 Subp3'1 KKKK. 7-6-2006]; 

voe: 2 PPMV NATURAL GAS 

(4) [RULE 1303(a)(l)-BACT, 

5-10-1996; RULE 1303(a)(I) 

-BACT, 12-6-2002] 

(2) (2A) (2B) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

A63.4, A99.6, 

Al9S.S, 

Al9S.9, 

Al9S. l0, 

AJ27. I, Cl.4, 

Cl.5, 029.7, 

OS2.3, OS2.4, 

EI93.6, 

El93.7, 

El93.ID, 

K67.6 

(S) (SA) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this pennit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D 

Facilitv ID: 

Revision#: 

Page· 21 

800074 

28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions . Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

CO OXIDATION CATALYST, BASF, Cl91 D189Cl92 

SS FOIL WITH ALUMINA 

WASHCOAT, MODEL CAMET, 80 

MODULES, CATALYST TOTAL 

VOLUME: 16-0 CUBIC FEET 

A/N:495991 

SELECTIVE CATALYTIC Cl92 Cl91 Sl94 NHJ: 5 PPMV (4) [RULE IJOJ(a) Dl2.9, 

REDUCTION, CORMETECH, MODEL: (l)·BACT, 5-I0-1996; RULE Dl2.IO, 

CMHT-27, WITH 12 MODULES, 121 I / 303(a)(l)-BACT, 12-6-2002] Dl2.ll, 

CU.FT. WITH 029.8, El79.5, 

A/N:495991 E179.6, 

El93.9 

AMMONIA INJECTION 

STACK, SERVING UNIT 16, HEIGHT: Sl94 Cl92 

150 FT: DIAMETER: 13 FT 6 IN 

A/N: 5596-05 

INTERNAL COMBUSTION ENGINE, D53 NOX: PROCESS NOX: 469 LBS/IOOO GAL B59.3, Cl.3, 

EMERGENCY POWER, DIESEL FUEL, UNIT** DIESEL (I) [RULE 2012, Cl77.I, 

ALCO, MODEL 251, 16 CYLINDERS, 5-ll-2001; RULE 2012, Dl2.5, Ell6.I, 

WITH AFTERCOOLER, 12-5-2003]: PM: (9) [RULE 404, El93.l I, 

TURBOCHARGER, 2500 HP WITH 2-7-1986] K67.5 

A/N: 451776 

GENERATOR, 2000 KW 

• (1) (lA) (I B) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (5A) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (8A) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits (IO) See section J for NESHAPIMACT requirements 

* * Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: .t..t. 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

INTERNAL COMBUSTION ENGINE. Dl95 NOX: PROCESS CO: 0.67 GRAM/BHP-HR (4) B6LI. Cl.6. 

EMERGENCY POWER. LEAN BURN. UNIT** [RULE 1703 - PSD Analysis, Dl2.12, 

#I, TURBOCHARGED, DIESEL FUEL. 10-7-1988; 40CFR 60 Subpart Dl2.13, 

CATERPILLAR MODEL 3516C. 1111, 7-11-2006]; NOX: 3.7 Ell6.2, 

WITH A JOHNSON MATTHEY CRT GRAM/BHP-HR (4) [RULE 1703 El93.6, 

PARTICULATE FILTER WITH HIGH - PSD Analysis, 10-7-1,88; E193.10, 

EFFICIENCY PARTICULATE AIR RULE 2005, H-2005]; NOX: 469 E448.I. 

FILTER. TURBOCHARGER, 3622 HP LBS/1000 GAL DIESEL (I) E448.2. 

WITH [RULE 2012, 5-6-2005]; PMlO: E448.3, K67.7 

A/N: 554366 0.007 GRAM/BHP-HR (4) [RULE 

1303(a)(l}-BACT, S-10-1996; 

RULE /303(a)(J)-BACT, 

12-6-2002]; voe: 02s 

GRAM/BHP-HR (4) [RULE 

1303(a)(l}-BACT, 5-10-1996; 

RULE /303(a)(J)-BACT, 

12-6-2002] 

TANK. DIESEL STORAGE, 2,800 E202 

GALLONS. SHARED WITH D 196 

• (I) (IA) (18) Denotes RECLAIM emission factor (2) (2A) (2B) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (5A) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS. NESHAPS, etc.) 

(9) See App B for Emission Limits (IO) See section J for NESHAP/MACT requirements 

• • Refer to section F and G of this permit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

Section D Page· 23 

Facilitv ID· 800074 

Revision#: 28 

Date: January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP BAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

INTERNAL COMBUSTION ENGINE, 

EMERGENCY POWER, LEAN BURN, 

#2, TURBOCHARGED, DIESEL FUEL, 

CATERPILLAR, MODEL 3516C, 

WITH A JOHNSON MATTHEY CRT 

PARTICULATE FILTER, WITH HIGH 

EFFICIENCY PARTICULATE AIR 

FILTER: TURBOCHARGER: 3622 HP 

WITH 

A/N: 554367 

Dl96 

TANK, DIESEL STORAGE, 2,800 E203 

GALLONS, SHARED WITH D 195 

STORAGE TANK, NO. I, AQUEOUS 

AMMONIA, CARBON STEEL, 38233 

GALS; DIAMETER: I4 FT; HEIGHT: 

38FT 61N 

A/N: 272086 

STORAGE TANK, NO. 2, AQUEOUS 

AMMONIA, CARBON STEEL, 38233 

GALS; DIAMETER: I4 FT; HEIGHT: 

38FT 6IN 

A/N: 272087 

D34 

D35 

• (1) (IA) (IB) Denotes RECLAIM emission factor 

C40 C4I 

C40C41 

(3) Denotes RECLAIM concentration limit 

(5) (5A) (SB) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

NOX: PROCESS 

UNIT** 

Emissions* 

And Requirements 

CO: 0.67 GRAM/BHP-HR (4) 

(RULE 1703-PSD Analysis, 

10-7-1988; 40CFR60 Subpart 

IIII, 7-11-2006]; NOX: 3.7 

GRAM/BHP-HR (4) [RULE 1703 

- PSD Analysis, 10-7-1988; 

RULE 2005, 5-6-2005]; NOX: 469 

LBS/1000 GAL (I) [RULE 2012, 

5-6-2005]; PM: 0.007 

GRAM/BHP-HR (4) [RULE 

1303(a)(l)-BACT, 5-10-1996; 

RULE /303(a)(1)-BACT, 

12-6-20021; voe: 0.25 

GRAM/BHP-HR (4) [RULE 

1303(a)(l)-BACT, 5-10-1996; 

RULE /303(a)(l)-BACT, 

12-6-2002] 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

861.1, CI.6, 

Dl2.12, 

Dl2.13, 

Ell6.2, 

E193.6, 

El93.IO, 

E448.l, 

E448.2, 

E448.3, K67.7 

CI57.I, 

EI44.I 

CI57.I, 

El44.l 

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(I 0) See section J for NESHAP/MACT requirements 

** Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 24 

Facilit)' ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected 

No. To 

STORAGE TANK. NO. 3, AQUEOUS 

AMMONIA, 3S233 GALS: 

DIAMETER: 14 FT: HEIGHT: 3S FT 6 

IN 

AIN:2720SS 

STORAGE TANK, NO. 4, AQUEOUS 

AMMONIA, 38233 GALS: 

DIAMETER: 14 FT: HEIGHT: 3S FT 6 

IN 

AIN: 2720S9 

STORAGE TANK, NO. 5, AQUEOUS 

AMMONIA, 3S233 GALS: 

DIAMETER: 14 FT: HEIGHT: 3S FT 6 

IN 

AIN:272090 

STORAGE TANK, NO. 6, AQUEOUS 

AMMONIA, 3S233 GALS: 

DIAMETER: 14 FT: HEIGHT: 3S FT 6 

IN 

AIN:272091 

SCRUBBER, PACKED BED, NO. I, 

VERTICAL PACKED TYPE, 

POLYPROPYLENE PACKING, 

HEIGHT: 9 FT 3 IN: DIAMETER: SIN 

AIN: 272090 

SCRUBBER, PACKED BED, NO. 2, 

VERTICAL PACKED TYPE, 

POLYPROPYLENE PACKING, 

HEIGHT: 9 FT 3 IN: DIAMETER: S IN 

AIN:272090 

STORAGE TANK, UNIT NO. I, 

MAGNESIUM COMPOUNDS, FUEL 

OIL ADDITIVE, 350 GALS 

AIN: 410730 

D36 

D37 

03S 

039 

C40 

C41 

021 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

C40C41 

C40C41 

C40C41 

C40C41 

034DJ5 036 

DJ7DJS 039 

D34 DJS D36 

DJ7 DJS 039 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (SB) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions* 

And Requirements 

(2) (2A) (28) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

Cl57.I, 

E144.l 

Ci57.I. 

El44.l 

El44.l 

Cl57.I, 

El44.I 

CS.I, Dl2.I, 

K67.2 

Dl2.I, K67.2 

(S) (8A) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(I 0) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this pennit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-4178 

Section D Page: 25 

Facilitv ID: 800074 

Revision # 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP BAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions . Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

'~ocel!ifSF · 1N.aacAN.BcHJlicAt'lfoiQ~1f , ______ ,-,- - ' -,~ - _,-_ - ,, -~, - "D'E''''' ~----~ 

STORAGE TANK. UNIT NO. 2, D22 

MAGNESIUM COMPOUNDS, FUEL 

OIL ADDITIVE, 350 GALS 

A!N:410732 

;.P;roc~~; P~~OL~~S~~~G~ -:2;;;.. •••••• . .. ·-.· FfiV ,;;,r]!:":: _,,g,,:• . :,_·,]::' .. . ;[,, 

STORAGE TANK, FIXED ROOF, D46 H23.I 

STEAM HEATED, NO. 172,003-A, 

FUEL OIL, 172000 BBL; DIAMETERi 

160 FT; HEIGHT! 48 FT 

A!N: C25861 

STORAGE TANK, FIXED ROOF, D47 H23.I 

STEAM HEATED, NO. 172,001-B, 

FUEL OIL, 172000 BBL; DIAMETER: 

160 FT; HEIGHT: 48 FT 

A/Ni C25859 

STORAGE TANK, FIXED ROOF, D48 H23.I 

STEAM HEATED, NO. 172.002-C, 

FUEL OIL, 172000 BBL; DIAMETER! 

160 FT; HEIGHT! 48 FT 

A/Ni C25860 

STORAGE TANK, FIXED ROOF, D49 H23.I 

STEAM HEATED, NO. 200,001-D, 

FUEL OIL, 200000 BBL; DIAMETERi 

160 FT; HEIGHT! 56 FT 

A/Ni C25862 

STORAGE TANK, FIXED ROOF, D50 H23.I 

STEAM HEATED, NO. 300,001-E, 

FUEL OIL, 300000 BBL; DIAMETER: 

200 FT; HEIGHT: 56 FT 

A/Ni C25863 

TANK, UNIT NO. I, TURBINE LUBE Dll C27 PM! (9) [RULE 404, 2-7-1986] 

OIL RESERVOIR 

A/Ni 122505 

• (I) (IA) ( IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits (10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 26 

Facilitv ID: 800074 

Revision#; 28 

Date: January 14. 201 S 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requirements 

Monitoring 

Unit 

~~ri'lces:~:q. PE"6Li:9'STO~·.::;s:••· ···n;:;::?'> ···::q:(~r·::;: ~,.:~ 

TANK, UNIT NO. I, TURBINE DI2 C27 PM: (9) [RULE 404, 2-7-1986] 

GOVERNOR OIL RESERVOIR 

A/N: 12250S 

ELECTROSTATIC PRECIPIT ATOR, C27 Dll DI2 0323.1 

NO. I, SMOG HOG, MODEL SH-I 0-PE, 

TWO STAGE, PENNY TYPE, 60 KW 

A/N: 122S05 

TANK, UNIT NO. 2, TURBINE LUBE 013 C28 PM: (9) [RULE 404, 2-7-1986] 

OIL RESERVOIR 

A/N: 122S06 

TANK, UNIT NO. 2, TURBINE 014 C28 PM: (9) [RULE 404,2-7-1986] 

GOVERNOR OIL RESERVOIR 

A/N: 122S06 

ELECTROSTATIC PRECIPIT ATOR, C28 Dl3 D14 0323.I 

NO. 2, SMOG HOG, MODEL SH-10-PE, 

TWOSTAGE,PENNYTYPE, 60KW 

A/N: 122506 

TANK, UNIT NO. 3. TURBINE LUBE DIS C29 PM: (9) [RULE 404,2-7-1986] 

OIL RESERVOIR 

A/N: 122S07 

TANK, UNIT NO. 3, TURBINE D16 C29 PM: (9) [RULE 404, 2-7-1986] 

GOVERNOR OIL RESER VOi R 

A/N: 122S07 

ELECTROSTATIC PRECIPIT ATOR, C29 DIS DI6 0323.1 

NO. 3, SMOG HOG, MODEL SH-10-PE, 

TWO STAGE, PENNEY TYPE, 60 KW 

A/N: 122S07 

TANK, UNIT NO. 4, TURBINE LUBE Dl7 C30 PM: (9) [RULE 404, 2-7-1986] 

OIL RESERVOIR 

A/N: 122S08 

TANK, UNIT NO. 4, TURBINE 018 C30 PM: (9) [RULE 404, 2-7-1986] 

GOVERNOR OIL RESERVOIR 

A/N: 122S08 

• (I) (IA) (IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (SA) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits (JO) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to detennine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 27 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

ELECTROSTATIC PRECIPIT A TOR. 

NO. 4. SMOG HOG, MODEL SH-10-PE, 

TWO STAGE, PENNEY TYPE, 60 KW 

NN·. 122508 

TANK, UNIT NO. 5, TURBINE LUBE 

OIL RESERVOIR 

NN: 122509 

ELECTROSTATIC PRECIPIT ATOR. 

NO. 5. SMOG HOG, MODEL SH-10-PE, 

TWO STAGE, PENNEY TYPE. 60 HP 

NN: 122509 

TANK, UNIT NO. 6, TURBINE LUBE 

OIL RESERVOIR 

NN: 1225!0 

ELECTROSTATIC PRECIPIT A TOR. 

NO. 6. SMOG HOG. MODEL SH-10-PE, 

TWO STAGE, PENNEY TYPE, 60 KW 

NN: 1225!0 

STORAGE TANK, FIXED ROOF, 

SETTLING TANK, LUBE 

OIL/WATER. VENTED TO 

ATMOSPHERE. 64()0 GALS; 

DIAMETER: 12 FT; HEIGHT; 8 FT 

WITH 

NN: 465115 

HEATER. I KW 

ID Connected 

No. To 

C30 Dl7 DI8 

Dl9 C31 

C31 DI9 

DIOO C32 

C32 OIOO 

Dll6 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions* 

And Requirements 

PM: (9) [RULE 404, 2-7-1986] 

PM: (9) [RULE 404, 2-7-1986] 

• (I) (IA) ( IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

Conditions 

D323.I 

D323.I 

D323.I 

H23.3 

(7) Denotes NSR applicability limit (8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits ( 10) See section J for NESl-IAPIMACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 28 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

STORAGE TANK, FIXED ROOF, 

RETENTION, LUBE OIL/WATER, 

VENTED TO ATMOSPHERE. 70 

GALS; DIAMETER: 2 FT; HEIGHT: 3 

FT SIN WITH 

A/N: 465115 

HEATER, I KW 

STORAGE TANK, FIXED ROOF. 

MECHANICAL SKIMMER. LUBE 

OIL/WATER. VENTED TO 

ATMOSPHERE, 595 GALS; 

DIAMETER: 4 FT 3.24 IN; HEIGHT: 5 

FT 71N 

AIN: 465115 

STORAGE TANK, FIXED ROOF, 

SKIM. LUBE OIL/WATER. VENTED 

TO ATMOSPHERE. 90GALS; 

WIDTH: I FT 6 IN; HEIGHT: 5 FT; 

LENGTH: 2FT 

A/N:465115 

SUMP. WASTE WATER. VENTED 

TO ATMOSPHERE. 3800 GALS; 

WIDTH: 6 FT; HEIGHT: 9 FT 8.4 IN; 

LENGTH: 8 FT 7 IN WITH 

A/N:465115 

PUMP, VENTED TO 

ATMOSPHERE 

SUMP. WASTE OIL, VENTED TO 

ATMOSPHERE, 4700GALS; WIDTH: 

5 FT 9.6 IN; HEIGHT: 9 FT 8.4 IN; 

LENGTH: II FT 6 IN 

A/N: 465115 

ID Connected 

No. To 

Dll8 

Dll9 

Dl20 

Dl22 

• (I) (IA) (IB) Denotes RECLAIM emission factor 

(3) Denotes RECLAIM concentration limit 

(5} (SA) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions* 

And Requirements 

(2) (2A) (2B) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

Conditions 

H23.3 

H23.3 

H23.3 

H23.3 

H23.3 

(8) (SA) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

( 10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to detennine the monitoring. recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D 

Facilitv ID: 

Revision#: 

Page: 29 

800074 

28 

Date: January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment ID Connected RECLAIM Emissions • Conditions 

No. To Source Type/ And Requiremeots 

Monitoring 

Unit 

!c~roc~~ ·(jjl!WA1'1:SEt5-tlQI~''•'~ :EE : .· ····''' .. ·. '·T·<:':·:.:· • ~ ~·.:"._.,,,,.,,, 

STORAGE TANK, WASTE WATER. Dl23 H23.3 

VENTED TO ATMOSPHERE, 6400 

GALS: DIAMETER: 12 FT; HEIGHT: 8 

FT WITH 

AIN: 465115 

HEATER. I KW 

SUMP.CONTAMINATED WATER. Dl54 H23.3 

COVERED, 3200 GALS; 2 TOTAL 

A/N: 465115 

TANK, BOILER FRONT WASTE, 250 0155 H23.3 

GALS 

AIN: 465115 

WASTE WATER SEPARATOR. #I, Dl98 

MAKE: HIGHLAND, MODEL: 

HTJ2000. 12000 GALS/HR; 2000 

GALS 

A/N: 495673 

WASTE WATER SEPARATOR, #2, Dl99 

MAKE: HIGHLAND, MODEL: 

HTJ2000, 12000 GALS/HR; 2000 

GALS 

A/N: 495674 

WASTE WATER SEPARATOR, #3, 0200 

MAKE: HIGHLAND, MODEL: 

HTJ2000, 12000 GALS/HR: 2000 

GALS 

AIN: 495675 

• (I) (IA) (IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate 

(3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit 

(5) (5A) (5B) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

(7) Denotes NSR applicability limit (8) (&A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(9) See App B for Emission Limits ( 10) See section J for NESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordk.eeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 30 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Equipment 

WASTE WATER SEPARATOR, 

MAKE: PSI, MODEL: PSC-I 000, 

UNDERGROUND, 6000 GALS/HR: 

!000 GALS: DIAMETER: 4 FT: 

LENGTil: I 5 FT 8 IN 

A/N: 53098I 

ABRASIVE BLASTING, OPEN, 

KELCO, MODEL I 24, 600 LBS 

CAPACITY, TWO NOZZLES, 

DIAMETER: .3 I IN 

A/N: I23I7I 

ID Connected 

No. To 

D20I 

D56 

SUMP, RAINWATER, 069 

UNDERGROUND, 420 BBL: WIDTH: 

I7FT 6 IN: DEPTH: 7 FT 9 IN: 

LENGTil: I7FT 6 IN 

RULE 2 I9 EXEMPT EQUIPMENT, 

ABRASIVE BLASTING EQUIPMENT, 

GLOVE-BOX,<= 53 FTJ, WITH DUST 

FILTER 

RULE 2 I 9 EXEMPT EQUIPMENT, 

AIR COND!TlONING UNITS 

RULE 2I9 EXEMPT EQUIPMENT, 

REFRIGERATION UNITS 

RULE 2 I9 EXEMPT EQUIPMENT, 

COATING EQUIPMENT, PORTABLE, 

ARCHITECTURAL COATINGS 

E112 

Ell3 

EII4 

EI24 

• (1) (IA) (IB) Denotes RECLAIM emission factor 

(3) Denotes RECLAIM concentration limit 

(5) (SA) (58) Denotes command and control emission limit 

(7) Denotes NSR applicability limit 

(9) See App B for Emission Limits 

RECLAIM 

Source Type/ 

Monitoring 

Unit 

Emissions• 

And Requirements 

PM: (9) [RULE 1140. 2-1-1980; 

RULE 1140, 8-2-1985; RULE 405. 

2-7-I986] 

PM: (9) [RULE 1146. 2-I-1980; 

RULE 1140, 8-2-1985; RULE 404, 

2-7-I986; RULE 405. 2-7-1986] 

Conditions 

D323.2 

0322.I, 

D38l.l, K67.I 

H23.5 

H23.6 

ROG: (9) [RULE 1113, 11-8-I996; K67.3 

RULE 1113, 7-13-2007; RULE 

1171, 11-7-2003; RULE 1171, 

2-1-2008] 

(2) (2A) (2B) Denotes RECLAIM emission rate 

(4) Denotes BACT emission limit 

(6) Denotes air toxic control rule limit 

(8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) 

(10) See section J forNESHAP/MACT requirements 

•• Refer to section F and G of this permit to determine the monitoring, recordkeeping and reporting requirements for this device. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Section D Page: 31 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: DEVICE ID INDEX 

The following sub-section provides an index 

to the devices that make u_p the facility 

description sorted by device ID. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 32 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: DEVICE ID INDEX 

DI I I I 

04 2 I I 

Oil 25 6 0 

012 26 6 0 

013 26 6 0 

014 26 6 0 

015 26 6 0 

016 26 6 0 

017 26 6 0 

018 26 6 0 

019 27 6 0 

021 24 5 0 

022 25 5 0 

C27 26 6 0 

C28 26 6 0 

C29 26 6 0 

C30 27 6 0 

C31 27 6 0 

C32 27 6 0 

034 23 5 0 

035 23 5 0 

036 24 5 0 

037 24 5 0 

038 24 5 0 

039 24 5 0 

C40 24 5 0 

C41 24 5 0 

046 25 6 0 

047 25 6 0 

048 25 6 0 

049 25 6 0 

050 25 6 0 

053 21 4 0 

056 30 8 0 

069 30 9 0 
,; 

South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 33 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: DEVICE ID INDEX 

Device Index For Section D 

D!l:~~' ID ;ii: S • DP ':No. · ..... ~~ .,;£f~~tell\,,~,; ; ; .. ;< ~ . ~· •.... ;;;jj;;;; _: __ -i[>_i;,.,I; •. ' -. ,' 

,-r"' ..... . ,_,,)hB£i>U·+ ·"' ''>~'°""·''::. ''""' ,. 

C73 I I I 

C74 I I I 

C75 2 I I 

C76 2 I I 

S96 2 I I 

S97 3 I I 

0100 27 6 0 

E 112 30 10 0 

El 13 30 10 0 

El 14 30 10 0 

DI 16 27 7 0 

0117 28 7 0 

0118 28 7 0 

0119 28 7 0 

0120 28 7 0 

0122 28 7 0 

0123 29 7 0 

El24 30 10 0 

0125 5 2 0 

0129 5 2 0 

Cl30 6 2 0 

CBI 6 2 0 

Sl33 6 2 0 

0134 8 2 0 

Cl38 9 2 0 

Cl39 9 2 0 

Sl41 9 2 0 

0142 8 2 0 

0154 29 7 0 

0155 29 7 0 

0159 10 3 0 

Cl61 11 3 0 

Cl62 11 3 0 

Sl64 11 3 0 

0165 12 3 0 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 34 

Facility ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: DEVICE ID INDEX 

Device Index For Section D 

3,,p~~· 

Cl67 

g fi1~~~~-1R.r~,~~.:-._,;:,1-;~~:1i 13 

!. ~··~ 3 0 

Cl68 13 3 0 

Sl70 13 3 0 

0171 14 3 0 

Cl73 15 3 0 

Cl74 15 3 0 

Sl76 15 3 0 

0177 16 3 0 

Cl79 17 3 0 

Cl80 17 3 0 

Sl82 17 3 0 

0183 18 3 0 

C185 19 3 0 

C186 19 3 0 

Sl88 19 3 0 

0189 20 3 0 

Cl91 21 3 0 

Cl92 21 3 0 

Sl94 21 3 0 

0195 22 4 0 

0196 23 4 0 

0198 29 7 0 

0199 29 7 0 

0200 29 7 0 

0201 30 7 0 

E202 22 4 0 

E203 23 4 0 
South Coast Air Quality Management District 

Z 1865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 35 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

FACILITY CONDITIONS 

F9. I Except for open abrasive blasting operations, the operator shall not discharge into the 

atmosphere from any single source of emissions whatsoever any air contaminant for a 

period or periods aggregating more than three minutes in any one hour which is: 

(a) As dark or darker in shade as that designated No. I on the Ringelmann Chart, as 

published by the United States Bureau of Mines; or 

(b) Of such opacity as to obscure an observer's view to a degree equal to or greater than 

does smoke described in subparagraph (a) of this condition. 

[RULE 401, 3-2-1984; RULE 40 I, 11-9-200 I) 

Fl4.I The operator shall not use fuel oil containing sulfur compounds in excess of 0.05 percent 

by weight. 

The .05 percent sulfur limit shall not apply to existing supplies of any liquid fuel in 

storage as of October I, 1993 until such supply is exhausted. 

[RULE 431.2, 5-4-1990; RULE 431.2, 9-15-2000) 

Fl4.2 The operator shall not purchase fuel oil containing sulfur compounds m excess of 15 ppm 

by weight as supplied by the supplier. 

This condition shall become effective on or after June I, 2004. 

[RULE 431.2, 9-15-2000) 

Fl6. I The operator shall keep records, in a manner approved by the District, for the following 

parameter( s) or item( s): 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 36 

Facilitv ID: 800074 

Revision #: 28 

Date: January 14. 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

purchase records of fuel oil and sulfur content of the fuel 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

F 18. l Acid Rain S02 Allowance Allocation for affected units are as follows: 

Device ID Boiler ID Contaminant Tons in any year 

I 

4 

71 

5 

7 

9 

BoilerNo. I S02 571 

Boiler No. 2 S02 328 

Boiler No. 3 S02 1131 

Boiler No. 4 S02 851 

Boiler No. 5 S02 1205 

Boiler No. 6 S02 1270 

a). The allowance allocation(s) shall apply to calendar years 2010 and beyond. 

b). The number of allowances allocated to Phase II affected units by U.S. EPA may 

change in a 1998 revision to 40CFR73 Tables 2,3, and 4. In addition, the number of 

allowances actually held by an affected source in a unit account may differ from the 

number allocated by U.S. EPA. Neither of the aforementioned conditions necessitate 

a rev1s1on to the unit S02 allowance allocations identified in this permit (see 40 CFR 

72.84) 

[40CFR 73 Subpart B, 1-11-1993] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 37 

Facility ID: 800074 

Revision#· 28 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

F24.I Accidental release prevention requirements of Section I 12(r)(7): 

a). The operator shall comply with the accidental release prevention requirements 

pursuant to 40 CFR Part 68 and shall submit to the Executive Officer, as a part of an 

annual compliance certification, a statement that certifies compliance with all of the 

requirements of 40 CFR Part 68, including the registration and submission of a risk 

management plan (RMP). 

b). The operator shall submit any additional relevant information requested by the 

Executive Officer or designated agency. 

[ 40CFR 68 - Accidental Release Prevention, 5-24-1996] 

DEVICE CONDITIONS 

A. Emission Limits 

A63.2 The operator shall limit emissions from this equipment as follows: 

CONTAMINANT 

co 

PMIO 

voe 

SOX 

EMISSIONS LIMIT 

Less than or equal to 18842 LBS IN ANY ONE MONTH 

Less than or equal to I 0784 LBS IN ANY ONE MONTH 

Less than or equal to 4409 LBS IN ANY ONE MONTH 

Less than or equal to 327 LBS IN ANY ONE MONTH 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

FACILITY PERMIT TO OPERATE 

Section D Page: 38 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall calculate the emission limit(s) by using calendar monthly fuel use 

data and the following emission factors: Natural Gas: PMI 0 = 7.50 lbs/MMscf, VOC 

= 2.58 lbs/MMscf, and SOx = 0.21 lbs/MMscf. Diesel Fuel: PMIO = 1.67 lbs/Mgal, 

VOC = 0.52 lbs/Mgal, and SOx = 0.21 lbs/Mgal. 

The operator shall calculate the emission limit(s) , after the CO CEMS certification, 

based on the readings from the certified CO CEMS. In the event the CO CEMS is not 

operating, has been certification tested but is not certified, or the emissions exceed 

the valid upper range of the analyzer, the emissions shall be calculated in accordance 

with the approved CEMS plan. During diesel readiness testing, the CO shall be 

calculated using the fuel use data and a 24.2 lbs/Mgal emission factor 

The operator shall calculate the emission limit(s) for CO in the absence of valid 

CEMS data, by using the monthly fuel use data and the following factor: Natural Gas: 

9.03 lbs/MMscf 

For the purposes of this condition, the limit(s) shall be based on the total combined 

emissions from combined cycle gas turbine No. I 0 and it's associated duct burner 

during any calendar month. The duct burner shall not be operated when the turbine is 

firing diesel fuel. 

(RULE 1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] 

[Devices subject to this condition: DJ34, Dl42] 

A63.3 The operator shall limit emissions from this equipment as follows: 

CONTAMINANT 

co 

PMIO 

voe 

SOX 

EMISSIONS LIMIT 

Less than or equal to 18842 LBS IN ANY ONE MONTH 

Less than or equal to I 0784 LBS IN ANY ONE MONTH 

Less than or equal to 4409 LBS IN ANY ONE MONTH 

Less than or equal to 327 LBS IN ANY ONE MONTH 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 39 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 201 S 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall calculate the emission limit(s) by using calendar monthly fuel use 

data and the following emission factors: Natural Gas: PMIO = 7.50 lbs/MMscf, VOC 

= 2.58 lbs/MMscf, and SOx = 0.21 lbs/MMscf. Diesel Fuel: PMIO = 1.67 lbs/Mgal, 

VOC = 0.52 lbs/Mgal, and SOx = 0.21 lbs/Mgal. 

The operator shall calculate the emission limit(s) , after the CO CEMS certification, 

based on the readings from the certi ed CO CEMS. In the event the CO CEMS is not 

operating, has been certification tested but is not certified, or the emissions exceed 

the valid upper range of the analyzer, the emissions shall be calculated in accordance 

with the approved CEMS plan. During diesel readiness testing, the CO shall be 

calculated using the fuel use data and a 24.2 lbs/Mgal emission factor 

For the purposes of this condition, the limit(s) shall be based on the total combined 

emissions from combined cycle gas turbine No. 9 and it' s associated duct burner 

during any calendar month. The duct burner shall not be operated when the turbine is 

firing diesel fuel. 

[RULE 1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] 

[Devices subject to this condition: D125, D129] 

A63.4 The operator shall limit emissions from this equipment as follows: 

CONTAMINANT 

co 

PMIO 

voe 

SOX 

EMISSIONS LIMIT 

Less than or equal to 11755 LBS IN ANY ONE MONTH 

Less than or equal to 3341 LBS IN ANY ONE MONTH 

Less than or equal to 2272 LBS IN ANY ONE MONTH 

Less than or equal to 90 LBS IN ANY ONE MONTH 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 40 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The above limits apply to each turbine. 

The operator shall calculate the emission limit(s) by using calendar monthly fuel use 

data and the following em1ss10n factors: VOC: 4.42 lbs/mmscf, PMIO: 6.5 

lbs/mmscf, SOx: 0.18 lbs/mmscf. 

The operator shall calculate the em1ss10n limits for CO after the CO CEMS 

certification based upon readings from the AQMD certified CEMS. In the event the 

CO CEMS is not operating or the emissions exceed the valid upper range of the 

analyzer, the emissions shall be calculated by using monthly fuel use data and the 

following factor: CO: 22.88 lbs/mmscf. 

[RULE 1303(b)(2)-0ffset, S-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] 

[Devices subject to this condition: Dl59, Dl65, DI 71, DI 77, Dl83, DI 89] 

A99. l The I 0 PPM NH3 emission limit(s) shall not apply when ammonia injection has not 

commenced. (NH3 emissions). 

[RULE 1303(a)(l)-BACT, S-10-1996; RULE l303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : C73, C75] 

A99.2 The 2 PPM NOX emission limit(s) shall not apply during turbine startups, diesel readiness 

testing, or shutdowns. Shutdowns shall not exceed 30 minutes/event. Written records of 

startups and shutdowns shall be maintained and made available to the AQMD upon request. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 41 

Facility ID: 800074 

Revision #: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

For the purposes of this condition, cold start up shall be defined as a start up which 

occurs after the steam turbine has been shutdown for 72 hours or more. A non-cold 

start up shall be defined as a start up which occurs after the steam turbine has been 

shutdown for less than 72 hours. The beginning of start up occurs at initial fire in the 

combustor and the end of start up occurs when the BACT levels are achieved. No 

more than one turbine shall be in cold start-up mode at any one time. The turbines 

shall not be started on diesel fuel. 

For the purposes of this condition, steam turbine shutdown period shall be defined as 

the number of hours between the closing and reopening of the steam stop valve. The 

operator shall keep records of the date and time of the steam stop valve opening and 

closing, and make these records available to AQMO personnel upon request. 

[RULE 2005, 5-6-2005] 

[Devices subject to this condition: Dl25, 0129, 0134, D142] 

A99.3 The 4 PPM CO emission limit(s) shall not apply during turbine startups, diesel readiness 

testing, or shutdowns. Shutdowns shall not exceed 30 minutes/event. Written records of 

startups and shutdowns shall be maintained and made available to the AQMO upon request. 

For the purposes of this condition, cold start up shall be defined as a start up which 

occurs after the steam turbine has been shutdown for 72 hours or more. A non-cold 

start up shall be defined as a start up which occurs after the steam turbine has been 

shutdown for less than 72 hours. The beginning of start up occurs at initial fire in the 

combustor and the end of start up occurs when the BACT levels are achieved. No 

more than one turbine shall be in cold start-up mode at any one time. The turbines 

shall not be started on diesel fuel. 

For the purposes of this condition, steam turbine shutdown period shall be defined as 

the number of hours between the closing and reopening of the steam stop valve. The 

operator shall keep records of the date and time of the steam stop valve opening and 

closing, and make these records available to AQMO personnel upon request. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 42 

Facility ID: 800074 

Revision#: 28 

Date: January 14,2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002) 

[Devices subject to this condition: D125, D129, D134, D142) 

A99.6 The 5.8 Lbs/hr PMIO emission limit(s) shall not apply during startup and shutdown 

periods .. 

[RULE 1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002) 

[Devices subject to this condition: Dl59, D165, Dl71, DI 77, D183, D189) 

A195.l The 2 PPMV NOX emission limit(s) is averaged over 60 minutes at 15 percent oxygen, 

dry. 

[RULE 2005, 5-6-2005) 

[Devices subject to this condition: D125, D129, Dl34, Dl42) 

Al95.2 The 4 PPMV CO emission limit(s) is averaged over 60 minutes, at 15 percent oxygen, dry. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002) 

[Devices subject to this condition: D125, D129, D134, D142) 

Al95.3 The 2 PPMV VOC emission limit(s) is averaged over 60 minutes, at 15 percent oxygen, 

dry. The limit does not apply during diesel readiness tests. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition: Dl25, D129, Dl34, Dl42) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 43 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Al95.4 The 5 PPMV NH3 emission limit(s) is averaged over 60 minutes at 15 percent 02 dry. 

The operator shall calculate and continuously record the NH3 slip concentration using the 

following: NH3(ppmv)=[a-b*c/1E6]*1E6/b, where a=NH3 injection rate (lb/hr)/17 

(lb/lb/mole), b=dry exhaust gas flow rate (lb/hr)/29(lb/lb/mole), and c=change in 

measured NOx across the SCR (ppmvd at 15 percent 02). The operator shall install and 

maintain a NOx analyzer to measure the SCR inlet NOx ppm accurate to within +/- 5 

percent calibrated at least once every 12 months. 

The operator shall use the method described above or another alternative method 

approved by the Executive Officer. 

The ammonia slip calculation procedures described above shall not be used for 

compliance determination or emission information determination without 

corroborative data using an approved reference method for the determination of 

ammonia. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subjectto this condition: Cl3 l, Cl39] 

A 195.5 The 5 PPMV NOX emission limit(s) is averaged over 720 operating hours (heat input 

weighted average). 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 44 

Facility ID· 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

A data acquisition system shall be installed and maintained to continuously calculate 

and record the NOx ppm based on the 720 operating hour average. 

The average shall be calculated based on emissions during all boiler operating hours 

except during: 

I. startups defined as whenever the unit is being brought up to normal operating 

temperature from an inactive status and the exhaust temperature entering the SCR 

catalyst is less than 530 degrees F; 

2. shutdowns defined as whenever the unit is allowed to cool from a normal 

operating temperature to inactive status and the exhaust temperature entering the SCR 

catalyst is less than 530 degrees F; 

3. calibration and maintenance periods, Part 75 linearity testing, RATA testing, 

equipment breakdown periods as defined in Rule 2004, and periods of zero fuel flow. 

The heat input weighted average NOx concentration shall be calculated using the 

following equation, or other equivalent equation. 

PPMV(3%02) = (Et/Qt)*K; where PPMV(3%02) = the concentration of NOx in 

PPMV at 3%02; K = a conversion factor from lbs/MMBtu to PPM, which can be 

determined using EPA 40 CFR60 Method 19. The default K value is 819; Et = Total 

reported NOx emissions during the averaging period including emissions reported as 

a result of missing data procedures pursuant to Rule 2012; Qt = Total heat input 

during the averaging period. 

[RULE 2009, 5-11-2001] 

[Devices subject to this condition : D 1, 04] 

Al95.8 The 2.5 PPMV NOX emission limit(s) is averaged over 1 hour, dry basis at 15 percent 

oxygen. This limit shall not apply during startup and shutdown periods. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 45 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subject to this condition: Dl59, Dl65, Dl71, DI 77, Dl83, Dl89] 

Al95.9 The 4 PPMV CO emission limit(s) is averaged over I hour, dry basis at 15 percent 

oxygen. This limit shall not apply during startup and shutdown periods. 

[RULE 1703 - PSD Analysis, 10-7-1988] 

[Devices subject to this condition: Dl59, Dl65, DI 71, DI 77, Dl83, Dl89] 

Al95.10 The 2 PPMV VOC emission limit(s) is averaged over I hour, dry basis at 15 percent 

oxygen. This limit shall not apply during startup and shutdown periods. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : D 159, Dl65, D 171, DI 77, DI 83, DI 89] 

A327.l For the purpose of determining compliance with District Rule 475, combustion 

contaminant emissions may exceed the concentration limit or the mass emission limit 

listed, but not both limits at the same time. 

[RULE 475, 10-8-1976; RULE 475, 8-7-1978] 

[Devices subject to this condition 

Dl77, Dl83, Dl89] 

Dl25, Dl29, Dl34, Dl42, Dl59, Dl65, Dl71, 

A433.l The operator shall comply at all times with the 2.0 ppm I hour BACT limit for NOx, 

except as specified in Conditions A99.2, and for the following operating scenarios:: 

Operating I Maximum Hourly Emission I Operational Limit 

Scenario Limit 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D Page: 46 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Cold Start I 225 lbs/hr 

Non-Cold Start I 170 lbs/hr 

[RULE 2005, 5-6-2005] 

I NOx emissions not to exceed 

600 lbs total per cold start. Cold 

start not to exceed 360 minutes 

total, 4 starts per month, and 48 

starts per year per turbine I NOx emissions not to exceed 

300 lbs total per non cold start. 

Non cold start not to exceed I 80 

minutes total, 27 starts per 

month, and 3 24 starts per year 

per turbine 

[Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] 

B. Material/Fuel Type Limits 

B59. l The operator shall only use the following material(s) in this device: 

Air preheater elements that are made of corrosion resistant stainless steel, type 409 

or equivalent 

A gunite lining in the flue gas duct surfaces between the air preheaters and exhaust 

stack, except for the turning vanes, expansion joints, and related parts 

[RULE 401, 3-2-1984; RULE 401, 11-9-2001] 

[Devices subject to this condition : DI, D4] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 47 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

B59.3 The operator shall only use the following material(s) in this device : 

Diesel which meets the specifications of Rule 431.2 

[RULE 431.2, 5-4-1990; RULE 431.2, 9-15-2000] 

[Devices subject to this condition : D53] 

B61.l The operator shall only use fuel oil containing the following specified compounds: 

Compound 

total sulfur 

compounds 

calculated as 

H2S 

is 

less than 

ppm by weight 

15 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 

6-3-2011; RULE 431.2, 5-4-1990; RULE 431.2, 9-15-2000] 

[Devices subject to this condition: 0195, Dl96] 

B75. l The operator shall not use fuel oil in this equipment except under the following 

circumstance(s ): 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page· 48 

Facility ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Interruption in natural gas service due to unforeseeable failure, malfunction, or 

natural disaster, not resulting from an intentional or negligent act or omission on the 

part of the owner or operator 

For diesel fuel readiness testing not to exceed 60 minutes per turbine per month. 

Fuel oil shall be low nitrogen, low sulfur diesel. Sulfur content shall not exceed 15 

ppm by weight, or other more stringent limit specified in Rule 431.2. The operator 

shall keep records of the date diesel was used, the amount of diesel used, and the 

reason for use. These records shall be kept for a minimum of 5 years and be made 

available for AQMD inspection upon request. 

Vendor specification for the initial and each subsequent shipment of diesel shall be 

maintained to verify sulfur and nitrogen content. If the vendor information is not 

available, the operator shall have a sample of each shipment of fuel analyzed by an 

independent lab for sulfur and nitrogen concentration. These records shall be kept for 

a minimum of 5 years and be made available for AQMD inspection upon request. 

For the above circumstances, diesel fuel shall not be used in this equipment unless 

water injection is fully employed. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 

4-9-1999; RULE 2005, 4-20-2001] 

[Devices subject to this condition: Dl25, Dl29, Dl34, D142] 

C. Throughput or Operating Parameter Limits 

C 1.3 The operator shall limit the operating time to no more than 199 hour(s) in any one year. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar. CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page· 49 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The 199 hours per year shall include no more than 50 hours m any one year for 

maintenance and testing purposes. 

The operation of the engine beyond the 50 hr/yr allotted for engine maintenance and 

testing shall be allowed only in the event of a loss of grid power or up to 30 minutes 

prior to a rotating outage, provided that the grid operator or electric utility has 

ordered rotating outages in the control area where the engine is located or has 

indicated that it expects to issue such an order at a certain time, and the engine is 

located in a utility service block that is subject to the rotating outage .. 

Engine operation shall be terminated immediately after the utility distribution 

company advises that a rotating outage is no longer imminent or in effect.. 

[RULE 1110.2, 2-1-2008; RULE 1470, 6-1-2007; RULE 2012, 5-6-2005] 

[Devices subject to this condition : D53] 

Cl .4 The operator shall limit the number of start-ups to no more than 150 in any one month. 

Startup time shall not exceed 25 minutes per startup. 

NOx emission shall not exceed 20 lbs per startup. 

For the purpose of this condition, a startup shall be defined as the start up process to 

bring the turbine in full successful operation that complies with the BACT emission 

limits. If during startup the process is aborted the process will count as one startup .. 

The operator shall determine NOx emissions in lbs for each startup based on CEMS 

data. The startup NOx emissions shall be recorded in the CEMS. 

The operator shall maintain records in a manner approved by the District, for a 

minimum of five year, to demonstrate compliance with this condition. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: SO 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subject to this condition: Dl59, Dl65, Dl71, DI 77, Dl83, Dl89] 

C 1.5 The operator shall limit the number of shut-downs to no more than 150 in any one month. 

Shutdown time shall not exceed I 0 minutes per shutdown. 

For the purposes of this condition, a shutdown event shall be defined as the period 

beginning with the initiation of the combustion turbine shutdown sequence and ending 

with the cessation of firing of the combustion' turbine engine. 

The operator shall maintain records in a manner approved by the District, for a 

minimum of five years, to demonstrate compliance with this condition. 

[RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subjectto this condition: Dl59, Dl65, Dl71, DI 77, Dl83, Dl89] 

C 1.6 The operator shall limit the operating time to no more than 200 hour(s) in any one year. 
South Coast Air Quality Management District 

21865 Copley Drive. Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 51 

Facilitv ID: 800074 

Revision#: 28 

Date: Janwuy 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operation includes no more than 50 hours per year and 4.2 hours per month for 

maintenance and testing as required in rule 14 70( c )(2). 

The operation includes 10 hours allowed for initial comrniss1onmg testing. The I 0 

hours commissioning operation shall not be included as part of the 50 hours per year 

operation for maintenance and testing. 

The operation of the engine beyond the50 hoursper year allotted for engme 

maintenance and testing shall be allowed only in the event of a loss of grid power or 

up to30 minutesprior to a rotating outage, provided that the electrical grid operator or 

electric utility has ordered rotating outages in the control area where the engine is 

located or has indicated that it expects to issue such an order at a certain time, and the 

engine is located in a utility service block that is subject to the rotating outage. 

Engine operation shall be terminated immediately after the utility distribution 

company advises that a rotating outage is no longer imminent or in effect. 

[RULE 1303(b)(l)-Modeling, 5-10-1996; RULE 1303(b)(l)-Modeling, 12-6-2002; 

RULE 1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002; RULE 1470, 

5-4-2012; 40CFR 60 Subpart fill, 7-11-2006] 

[Devices subject to this condition : D 195, D 196] 

CS. I The operator shall use this equipment in such a manner that the flow rate being monitored, 

as indicated below, is not less than 2.5 gpm. 

To comply with this condition, the operator shall monitor the flow rate as specified 

in condition number 12-1. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a){l)-BACT, 12-6-2002] 

[Devices subject to this condition : C40] 

C 157. I The operator shall install and maintain a pressure relief valve set at 15 psig. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 52 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 402, 5-7-1976] 

[Devices subject to this condition: D34, D35, D36, D37, D39] 

C 177. I The operator shall set and maintain the fuel injection timing of the engme at 4 degrees 

retarded relative to standard timing. 

[RULE 2009, 5-11-2001] 

[Devices subject to this condition : D53] 

D. Monitoringffesting Requirements 

Dl2.I The operator shall install and maintain a(n) flow meter to accurately indicate the flow rate 

of the incoming scrubbing (city) water. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)( 1)-BACT, 12-6-2002] 

[Devices subject to this condition: C40, C41] 

Dl2.2 The operator shall install and maintain a(n) temperature gauge to accurately indicate the 

temperature at the inlet of each selective catalytic reduction reactor. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 

5-11-2001; RULE 2012, 12-5-2003] 

[Devices subject to this condition : C73, C75] 

D12.3 The operator shall install and maintain a(n) continuous monitoring system to accurately 

indicate the ammonia injection rate of the ammonia injection system. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 53 

Facility ID: 800074 

Revision#: 28 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall also install and maintain a device to continuously record the 

parameter being measured. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : C73, C75] 

D 12.5 The operator shall install and maintain a(n) non-resettable elapsed time meter to 

accurately indicate the elapsed operating time of the engine. 

[RULE 1110.2, 2-1-2008; RULE 2012, 5-6-2005] 

[Devices subject to this condition : D53] 

D12.6 The operator shall install and maintain a(n) temperature gauge to accurately indicate the 

temperature in the exhaust at the inlet to the SCR reactor. 

The operator shall also install and maintain a device to continuously record the 

parameter being measured. 

The measuring device or gauge shall be accurate to within plus or minus 5 percent. It 

shall be calibrated once every 12 months. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 

5-11-2001; RULE 2012, 12-5-2003] 

[Devices subject to this condition : C 131, C 139] 

012.7 The operator shall install and maintain a(n) pressure gauge to accurately indicate the 

differential pressure across the SCR catalyst bed in inches of water column. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 54 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall also install and maintain a device to continuously record the 

parameter being measured. 

The measuring device or gauge shall be accurate to within plus or mmus 5 percent. It 

shall be calibrated once every 12 months. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 

5-11-2001; RULE 2012, 12-5-2003] 

[Devices subject to this condition : C 131, C 139] 

012.8 The operator shall install and maintain a(n) continuous monitoring system to accurately 

indicate the ammonia injection rate of the ammonia injection system. 

The operator shall also install and maintain a device to continuously record the 

parameter being measured. 

The measuring device or gauge shall be accurate to within plus or minus 5 percent. It 

shall be calibrated once every 12 months. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : C 131, C 139] 

D 12.9 The operator shall install and maintain a(n) flow meter to accurately indicate the flow rate 

of the total hourly throughput of injected ammonia (NH3). 

The operator shall also install and maintain a device to continuously record the 

parameter being measured. 

The measuring device or gauge shall be accurate to within plus or minus 5 percent. 

The accuracy of the device shall be verified once every 12 months. 

The ammonia injection rate shall remain between 74.9 and 143.9 lbs per hour. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 55 

Facility ID: 800074 

Revision#: 28 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1703 - PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subjectto this condition : C 162, Cl 68, Cl 74, C 180, C 186, Cl 92] 

Dl2.IO The operator shall install and maintain a(n) temperature gauge to accurately indicate the 

temperature at the inlet to the SCR reactor. 

The operator shall also install and maintain a device to continuously record the 

parameter being measured. 

The measuring device or gauge shall be accurate to within plus or minus 5 percent. 

The accuracy of the device shall be verified once every 12 months. 

Ammonia injection shall be used at all times at an injection rate which minimizes 

NOX emissions whenever the exhaust temperature prior to the inlet of the SCR 

catalyst is between 734 F and 850 F as measured by the temperature gauge. 

[RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subject to this condition: Cl62, Cl68, Cl 74, Cl80, Cl86, Cl92] 

Dl2. I I The operator shall install and maintain a(n) pressure gauge to accurately indicate the 

differential pressure across the SCR catalyst bed in inches water column. 

The operator shall also install and maintain a device to continuously record the 

parameter being measured. 

The measuring device or gauge shall be accurate to within plus or minus 5 percent. 

The accuracy of the device shall be verified once every 12 months. 

The pressure differential shall be between 4.0 and 5.8 inches water column. 

[RULE 1703 - PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 56 

Facilitv ID· 800074 

Revision#· 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[Devices subject to this condition: Cl62, Cl68, Cl 74, Cl80, Cl86, Cl92] 

Dl2.12 The operator shall install and maintain a(n) non-resettable elapsed time meter to 

accurately indicate the elapsed operating time of the engine. 

[RULE 1304(c)-Offset Exemption, 6-14-1996; RULE 1470, 6-1-2007; 40CFR 60 

Subpart 1111, 7-11-2006] 

[Devices subject to this condition: Dl95, Dl96] 

Dl2.13 The operator shall install and maintain a(n) non-resettable totalizing fuel flow meter to 

accurately indicate the fuel usage of the engine. 

[RULE 2012, 5-6-2005] 

[Devices subject to this condition : D 195, D 196] 

D28.3 The operator shall 

specifications: 

conduct source test(s) in accordance with the following 
South Coast Air Quality Management District 

21865 Copley Drive. Diamond Bar, CA 91765-4178 

Section D 

Facilitv ID· 

Revision#: 

Page: 57 

800074 

28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The test shall be conducted quarterly during the first 12 months after the initial 

source test, and once a year thereafter. 

The District shall be notified of the date and time of the test at least 7 days pnor to 

the test. 

Source test shall be conducted when this equipment is using natural gas. 

The test shall be conducted by a testing laboratory certified by the California Air 

Resources Board in the required test methods , and in compliance with District Rule 

304 (no conflict of interest). 

The test shall be conducted to determine the NH3 emissions usmg District method 

207.1 measured over a 60 minute averaging time period. 

The test shall be conducted to determine the NH3 emissions using either District 

method 5.3 or EPA method 17 measured over a 60 minute averaging time period. 

The test shall be conducted when the equipment is operating at 80 percent load or 

greater. 

The test shall be conducted and the results submitted to the District within 45 days 

after the test date. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : C73, C75] 

D29.2 The operator shall conduct source test(s) for the pollutant(s) identified below. 

Pollutant(s) to 

be tested 

I Required Test Method(s) I Averaging Time I Test Location 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 58 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

NH3 emissions District method 207 .1 

and 5.3 or EPA method 

17 

I 1 hour I Outlet of the SCR 

serving this equipment 

The test(s) shall be conducted at least once each calendar quarter during the first 12 

months of operation and at least annually thereafter. The NOx concentration, as 

detennined by the CEMS, shall be simultaneously recorded during the ammonia slip 

test. If the CEMS is inoperable, a test shall be conducted to detennine the NOx 

emissions using District Method 100. l measured over a 60 minute averaging time 

period. 

The test shall be conducted to demonstrate compliance with the Rule 1303 

concentration limit. 

The test shall be conducted when the equipment is operating at 80 percent load or 

greater. 

The test shall be conducted and the results submitted to the AQMD pennitting 

engineer within 45 days after the test date. 

The test shall be conducted during natural gas firing. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : C 131, C 139] 

D29.4 The operator shall conduct source test(s) for the pollutant(s) identified below. 

Pollutant(s) to 

be tested 

SOX emissions 

Required Test Method(s) 

Approved District method 

I Averaging Time 

District-approved 

averaging time 

I Test Location 

Fuel sample 
South Coast Air Quality Management District 

21865 Copley Drive. Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Section D Page: 59 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

ROG emissions 

PMIO 

emissions 

Approved District method 

District method 5.2 

I hour 

District-approved 

averaging time 

The test(s) shall be conducted at least once every three years. 

I Outlet of the SCR 

serving this equipment I Outlet of the SCR 

serving this equipment 

For gas turbines only the VOC test shall use the following method: a) Stack gas 

samples are extracted into Summa canisters, maintaining a final canister pressure 

between 400-500 mm Hg absolute, b) Pressurization of Summa canisters is done 

with zero gas analyzed/certified to having less than 0.05 ppmv total hydrocarbons as 

carbon, and c) Analysis of Summa canisters is per EPA Method T0-12 (with 

pre-concentration) and the canisters temperature when extracting samples for 

analysis is not to be below 70 deg F. 

The use of this alternative VOC test method is solely for the determination of 

compliance with the VOC BACT level of 2.0 ppmv calculated as carbon for natural 

gas fired turbines. Because the BACT level was set using data derived from various 

source test methods, this alternate method provides a fair comparison and represents 

the best sampling and analysis technique for this purpose at this time. The test results 

must be reported with two significant digits. 

The test shall be conducted and the results submitted to the AQMD within 60 days 

after the test date. The AQMD shall be notified of the date and time of the test at 

least 7 days prior to the test. 

The test shall be conducted to demonstrate compliance with the Rule 1303 

concentration and emissions limit. 

The test shall be conducted when the turbine and duct burner are operating 

simultaneously at I 00 percent of full rated load, when the turbine is operating alone 

at I 00 percent of full rated load, and when the turbine is operating alone at 75 and 50 

percent of full rated load for NOx, CO, ROG, and NH3 source tests. 

The test shall be conducted when firing natural gas. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 60 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 

1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] 

[Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] 

D29.5 The operator shall conduct source test(s) for the pollutant(s) identified below. 

Pollutant(s) to 

be tested 

NOX emissions 

Required Test Method(s) 

District method 100.1 

I Averaging Time 

30 minutes 

I Test Location 

Outlet of the SCR 

serving this equipment 

The test shall be conducted when the unit is firing diesel fuel in order to determine 

the emissions profile of the unit. A minimum of 6 tests shall be performed and the 

operator shall record the turbine output, ammonia injection rate, and temperature of 

the exhaust during each test, based on a 30 minute averaging time. Test results shall 

also include the fuel flow rate (CFH), the flue gas flow rate, and the duct burner fuel 

use during the test. 

The test shall be conducted in order to generate a load curve for NOx (lbs/MW) vs. 

MW output over the span of tested loads. The operator may, after receiving approval 

from the AQMD, use this curve to report NOx emissions during the monthly 60 

minute (total) diesel readiness testing periods. 

[RULE 2012, 5-6-2005] 

[Devices subject to this condition: Dl25, D129, Dl34, Dl42] 

D29.7 The operator shall conduct source test(s) for the pollutant(s) identified below. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 61 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Pollutant(s) to Required Test Method(s) Averaging Time I Test Location 

be tested 

SOX emissions Approved District method I hour Fuel Sample 

voe emissions Approved District method I hour Outlet of the SCR 

serving this equipment 

PMIO Approved District method District-approved I Outlet of the SCR 

emissions averaging time serving this equipment 

PM2.5 Approved District method District-approved I Outlet of the SC R 

averaging time serving this equipment 

The test(s) shall be conducted at least once every three years. 

The test shall be conducted and the results submitted to the District within 90 days 

after the test date. The AQMD shall be notified of the date and time of the test at 

least I 0 days prior to the test .. 

The test shall be conducted when the gas turbine is operating at I 00 percent of 

maximum heat input.. 

For gas turbines only the VOC test shall use the following method: a) Stack gas 

samples are extracted into Summa canisters, maintaining a final canister pressure 

between 400-500 mm Hg absolute, b) Pressurization of Summa canisters is done 

with zero gas analyzed/certified to having less than 0.05 ppmv total hydrocarbons as 

carbon, and c) Analysis of Summa canisters is per EPA Method T0-12 (with 

pre-concentration) and the canisters temperature when extracting samples for 

analysis is not to be below 70 degrees 

The use of this alternative VOC test method is solely for the determination of 

compliance with the VOC BACT level of 2.0 ppmv calculated as carbon for natural 

gas fired turbines. The test results must be reported with two significant digits. 

The test shall be conducted to demonstrate compliance with the Rule 1303 

concentration and/or monthly emissions limit. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 62 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 

1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] 

[Devices subjectto this condition: Dl59, Dl65, DI 71, DI 77, Dl83, Dl89] 

D29.8 The operator shall conduct source test(s) for the pollutant(s) identified below. 

Pollutant(s) to 

be tested 

NH3 emissions 

Required Test Method( s) 

District method 207.1 or 

EPA method 17 

Averaging Time 

I hour 

I Test Location 

Outlet of the SCR 

serving this equipment 

The test shall be conducted and the results submitted to the District within 90 days 

after the test date. The AQMD shall be notified of the date and time of the test at 

least I 0 days prior to the test.. 

The test(s) shall be conducted at least quarterly during the first twelve months of 

operation and at least annually thereafter. The NOx concentration, as determined by 

the certified CEMS, shall be simultaneously recorded during the ammonia slip test. If 

the CEMS is inoperable or not yet certified, a test shall be conducted to determine 

the NOx emissions using District Method I 00.1 measured over a 60 minute 

averaging time period .. 

The test shall be conducted to demonstrate compliance with the Rule 1303 

concentration limit.. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subjecttothis condition: C73, C75, Cl62, Cl68, Cl74, Cl80, Cl86, Cl92] 

D82. I The operator shall install and maintain a CEMS to measure the following parameters: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 63 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

CO concentration in ppmv 

Concentrations shall be corrected to 15 percent oxygen on a dry basis. 

The CEMS will convert the actual CO concentrations to mass emission rates (lbs/hr) 

and record the hourly emission rates on a continuous basis. 

The CEMS shall be installed and operated no later than 90 days after initial start up 

of the turbine, and in accordance with an approved AQMD Rule 218 CEMS plan 

application. The operator shall not install the CEMS prior to receiving initial approval 

from AQMD. Within two weeks of the turbine start up date, the operator shall 

provide written notification to the AQMD of the exact start up. 

The CEMS shall be installed and operated to measure CO concentration over a 15 

minute averaging time period. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 218, 

8-7-1981; RULE 218, 5-14-1999) 

[Devices subject to this condition: 0125, 0129, 0134, 0142) 

082.2 The operator shall install and maintain a CEMS to measure the following parameters: 

NOX concentration in ppmv 

Concentrations shall be corrected to 15 percent oxygen on a dry basis. 

The CEMS shall be installed and operated no later than 12 months after initial start 

up of the turbine and shall comply with the requirements of Rule 2012. During the 

interim period between the initial start up and the provisional certification date of the 

CEMS, the operator shall comply with the monitoring requirements of Rule 2012(h) 

(2) and 2012(h)(3). Within two weeks prior to the turbine start up date, the operator 

shall provide written notification to the AQMD of the exact date of start up. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 64 

F'acilitv ID: 800074 

Revision#: 28 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 2012, 5-6-2005] 

[Devices subject to this condition: 0125, 0129, 0134, 0142] 

082.3 The operator shall install and maintain a CEMS to measure the following parameters: 

CO concentration in ppmv 

Concentrations shall be corrected to 15 percent oxygen on a dry basis. 

The CEMS shall be installed and operated to measure CO concentration over a 15 

minute averaging time period. 

The CEMS shall be installed The CEMS shall be operated m accordance with an 

approved AQMO Rule 218 CEMS plan application. 

The CEMS will convert the actual CO concentrations to mass em1ss10n rates (lbs/hr) 

and record the hourly emission rates on a continuous basis. 

CO Emission Rate, lbs/hr = K*Cco*Fd[20.9/(20.9% - %02 d)][(Qg * HHV)/106], 

where 

I. K = 7 .267 * l 0-8 (lb/sct)/ppm 

2. Ceo = Average of four consecutive 15 min. average CO concentration, ppm 

3. Fd = 8710 dscf/MMBTU natural gas 

4. %02 d =Hourly average% by vol. 02 dry, corresponding to Ceo 

5. Qg =Fuel gas usage during the hour, scf/hr 

6. HHV = Gross high heating value of fuel gas, BTU/scf 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 218, 

8-7-1981; RULE 218, 5-14-1999] 
South Coast Air Quality Management District 

21865 Copley Drive. Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 65 

Facility ID: 800074 

Revision#: 28 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[Devices subject to this condition: Dl59, Dl65, Dl71, DI 77, Dl83, Dl89] 

D82.4 The operator shall install and maintain a CEMS to measure the following parameters: 

NOX concentration in ppmv 

Concentrations shall be corrected to 15 percent oxygen on a dry basis. 

The CEMS shall be installed and operated no later than 90 days after initial start-up 

of the turbine, and in accordance with an approved AQMD Rule 218 CEMS plan 

application. The operator shall not install the CEMS prior to receiving initial approval 

fromAQMD. 

[RULE 2012, 5-6-2005] 

[Devices subject to this condition: Dl59, D165, D171, DI 77, Dl83, Dl89] 

Dl82. l The operator shall test this equipment in accordance with the following specifications: 

The operator shall collect samples using a 1983 District-approved induct fallout 

monitor (!FM) every 24 hours beginning from all startups, except for natural gas 

firing, where if three 24-hour !FM samples show no abnormal collection, subsequent 

samples can be taken once a week. 

The operator shall analyze the !FM samples for acidity, weight, increase of particle 

size, volume, and appearance, and use the results of the analysis to determine the 

necessary operational changes to minimize the fallouts, such as, but not limited to, 

increasing the fuel oil additives and lancing frequencies. 

[RULE 401, 3-2-1984; RULE 401, 11-9-2001] 

[Devices subject to this condition: DI, D4] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 66 

Facility ID: 800074 

Revision #: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

0322.1 The operator shall perform annual inspection of the equipment and filter media for leaks, 

broken or tom filter media, and improperly installed filter media. 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition : E 112] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 67 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

D323. l The operator shall conduct an inspection for visible emissions from all stacks and other 

emission points of this equipment whenever there is a public complaint of visible 

emissions, whenever visible emissions are observed, and on a daily basis, at least, unless 

the equipment did not operate during the entire daily period. The routine daily inspection 

shall be conducted while the equipment is in operation and during daylight hours. 

If any visible emissions (not including condensed water vapor) are detected that last more 

than three minutes in any one hour, the operator shall verify and certify within 24 hours 

that the equipment causing the em1ss1on and any associated air pollution control 

equipment are operating normally according to their design and standard procedures and 

under the same conditions under which compliance was achieved in the past, and either: 

1 ). Take corrective action(s) that eliminates the visible emissions within 24 hours and 

report the visible emissions as a potential deviation in accordance with the reporting 

requirements in Section K of this permit; or 

2). Have a CARE-certified smoke reader determine compliance with the opacity 

standard, using EPA Method 9 or the procedures in the CARB manual "Visible Emission 

Evaluation", within three business days and report any deviations to AQMD. 

SUGGESTED CHAR 

The operator shall keep the records in accordance with the recordkeeping requirements m 

Section K of this permit and the following records: 

I). Stack or emission point identification; 

2). Description of any corrective actions taken to abate visible emissions; 

3). Date and time visible emission was abated; and 

4). All visible emission observation records by operator or a certified smoke reader. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Section D Page: 68 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition: C27, C28, C29, C30, C31, C32] 
South Coast Air Quality Management District 

Z 1865 Copley Drive, Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Section D Page: 69 

Facility ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

D323.2 The operator shall conduct an inspection for visible emissions from all stacks and other 

emission points of this equipment whenever there is a public complaint of visible 

emissions, whenever visible emissions are observed, and on a semi-annual basis, at least, 

unless the equipment did not operate during the entire semi-annual period. The routine 

semi-annual inspection shall be conducted while the equipment is in operation and during 

daylight hours. 

If any visible em1ss1ons (not including condensed water vapor) are detected that last more 

than three minutes in any one hour, the operator shall verify and certify within 24 hours 

that the equipment causing the em1ss1on and any associated air pollution control 

equipment are operating normally according to their design and standard procedures and 

under the same conditions under which compliance was achieved in the past, and either: 

1 ). Take corrective action(s) that eliminates the visible emissions within 24 hours and 

report the visible emissions as a potential deviation in accordance with the reporting 

requirements in Section K of this permit; or 

2). Have a CARB-certified smoke reader determine compliance with the opacity 

standard, using EPA Method 9 or the procedures in the CARB manual "Visible Emission 

Evaluation", within three business days and report any deviations to AQMD. 

The operator shall keep the records in accordance with the recordkeeping requirements in 

Section K of this permit and the following records: 

1 ). Stack or emission point identification; 

2). Description of any corrective actions taken to abate visible emissions; 

3). Date and time visible emission was abated; and 

4). All visible emission observation records by operator or a certified smoke reader. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 70 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition : D56] 

D371.I The operator shall conduct an inspection for visible em1ss10ns from all stacks and other 

emission points of this equipment whenever this equipment has combusted one million 

gallons of diesel fuel, to be counted cumulatively over a five year period. The inspection 

shall be conducted while the equipment is in operation and during daylight hours. If any 

visible emissions (not including condensed water vapor) are detected, the operator shall: 

Have a CARS-certified smoke reader determine compliance with the opacity standard, 

using EPA Method 9 or the procedures in the CARB manual "Visible Emission 

Evaluation", within three working days (or during the next fuel oil firing period if the unit 

ceases firing on fuel oil within the three working day time frame) and report any 

deviations to AQMD. 

In addition, the operator shall keep the records in accordance with the recordkeeping 

requirements in Section K of this permit and the following records: 

a). Stack or emission point identification; 

b ). Description of any corrective actions taken to abate visible emissions; 

c). Date and time visible emission was abated; and 

d). Visible emission observation record by a certified smoke reader. 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition: DI, 04] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 71 

Facility ID: 800074 

Revis.ion#: 28 

Date: Janlllll)' 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

0372.1 The operator shall determine compliance with the particulate matter (PM) em1ss1on limit 

by conducting a source test at the outlet of the exhaust stack annually using AQMD 

Method 5.1. Each test shall include: 

(a) One test using natural gas operating at mm1mum load under normal operating 

conditions, if natural gas is burned more than 120 consecutive hours or 200 hours 

accumulated over any 12 consecutive months. The test shall be conducted no later than six 

months after the time limit has been exceeded; 

(b) One test using natural gas operating at maximum load under normal operating 

conditions, if natural gas is burned more than 120 consecutive hours or 200 hours 

accumulated over any 12 consecutive months. The test shall be conducted no later than six 

months after the time limit has been exceeded; 

( c) One test using fuel oil operating at maximum load under normal operating conditions, 

if fuel oil is burned more than 120 consecutive hours or 200 hours accumulated over any 

twelve consecutive months. The test shall be conducted no later than six months after the 

time limit has been exceeded. 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition: 0125, 0129, 0134, 0142] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 72 

Facility ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

D381. l The operator shall conduct an inspection for visible emissions from all stacks and other 

emission points of this equipment whenever there is a public complaint of visible 

em1ss10ns, whenever visible emissions are observed, and on an annual basis, at least, 

unless the equipment did not operate during the entire annual period. The routine annual 

inspection shall be conducted while the equipment is in operation and during daylight 

hours. If any visible emissions (not including condensed water vapor) are detected, the 

operator shall take corrective action(s) that eliminates the visible emissions within 24 

hours and report the visible emissions as a potential deviation in accordance with the 

reporting requirements in Section K of this permit. 

The operator shall keep the records in accordance with the recordkeeping requirements m 

Section K of this permit and the following records: 

1 ). Stack or emission point identification; 

2). Description of any corrective actions taken to abate visible emissions; and 

3). Date and time visible emission was abated. 

[RULE 3004(a){4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition : E 112] 

E. Equipment Operation/Construction Requirements 

E57.1 The operator shall vent this equipment to the SCR and CO control whenever this 

equipment is in operation. 

Ammonia injection shall be used at all times at an injection rate which minimizes 

NOx emissions whenever the exhaust temperature prior to the inlet of the SCR 

catalyst is 450 degrees F or greater as measured by the temperature gauge required 

by condition Dl2.6 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 73 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 

4-20-2001; RULE 2005, 5-6-2005] 

[Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] 

E73. l Notwithstanding the requirements of Section E conditions, the operator shall not use 

ammonia injection if any of the following requirement(s) are met: 

I. Whenever the inlet exhaust temperature prior to the SCR reactor is less than 530 

degrees Fahrenheit. 

[RULE 2012, 5-11-2001; RULE 2012, 12-5-2003] 

[Devices subject to this condition : C73, C75] 

E73.2 Notwithstanding the requirements of Section E conditions, the operator may, at his 

discretion, choose not to use ammonia injection if all of the following requirement(s) are 

met: 

The inlet exhaust temperature to the SCR is 450 degrees F or less, not to exceed 360 

minutes during a cold startup or 180 minutes during a non-cold startup. 

During diesel readiness testing. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 

4-9-1999; RULE 2005, 4-20-2001] 

[Devices subject to this condition : C 131, C 139] 

E 116.1 This engine shall not be used as part of a demand response program usmg interruptible 

service contract in which a facility receives a payment or reduced rates in return for 

reducing its electric load on the grid when requested to do so by the utility or the grid 

operator. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 74 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 1470, 6-1-2007] 

[Devices subject to this condition : D53] 

E 116.2 This engine shall not be used as part of a demand response program using interruptible 

service contract in which a facility receives a payment or reduced rates in return for 

reducing its electric load on the grid when requested to do so by the utility or the grid 

operator. 

[RULE 1470, 5-4-2012] 

[Devices subject to this condition : D 195, D 196] 

E 144.1 The operator shall vent this equipment, during filling, only to the vessel from which it 1s 

being filled. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : D34, D35, D36, D37, D38, D39] 

El79.l For the purpose of the following condition number(s), "continuous monitoring" shall be 

defined as measuring at least once every 15 minutes, except as allowed by Rule 2000. 

Condition Number D 12- 3 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition : C73, C75] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 75 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

El 79.2 For the purpose of the following condition number(s), "continuously record" shall be 

defined as recording at least once every hour and shall be calculated based upon the 

average of the continuous monitoring for that hour. 

Condition Number D 12- 3 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 

5-11-2001; RULE 2012, 12-5-2003] 

[Devices subject to this condition : C73, C75] 

El79.3 For the purpose of the following condition number(s), continuously record shall be 

defined as recording at least once every hour and shall be calculated upon the average of 

the continuous monitoring for that month. 

Condition Number D 12- 7 

[RULE 1303(a){l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 

5-11-2001; RULE 2012, 12-5-2003] 

[Devices subject to this condition : C 131, C 139] 

E 179.4 For the purpose of the following condition number(s), continuously record shall be 

defined as recording at least once every hour and shall be calculated upon the average of 

the continuous monitoring for that hour. 

Condition Number D 12- 6 

Condition Number D 12- 8 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 

5-11-2001; RULE 2012, 12-5-2003] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 76 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[Devices subject to this condition : C 13 1, C 139] 

El 79.5 For the purpose of the following condition number(s), continuously record shall be 

defined as recording at least once every 15 minutes and shall be calculated based upon the 

average of the continuous monitoring for that hour .. 

Condition Number D 12- 9 

[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1703 

-PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subject to this condition: Cl62, Cl68, Cl 74, Cl80, C!86, Cl92] 

El 79.6 For the purpose of the following condition number(s), continuously record shall be 

defined as at least once every hour and shall be calculated based upon the average of the 

continuous monitoring for that month. 

Condition Number D 12-10 

Condition Number D 12-11 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 

5-6-2005] 

[Devices subject to this condition : C 162, C168, Cl 74, Cl80, C 186, Cl92] 

E 193. l The operator shall upon completion of construction, operate and maintain this equipment 

according to the following specifications: 

Jn compliance with all mitigation measures as stipulated by the "Statement of 

Findings, Statement of Overriding Considerations, and Mitigation Monitoring Plan" 

and final Environmental Impact Report dated July 16, 2002 (SCH No. 

20011121013), and addendum to the FEIR 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 77 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall com ply with the terms and conditions set forth below: 

[CA PRC CEQA, 11-23-1970] 

[Devices subject to this condition: 0125, 0129, 0134, 0142] 

El93.6 The operator shall upon completion of construction, operate and maintain this equipment 

according to the following specifications: 

In accordance with all air quality mitigation measures stipulated in the Environmental 

Impact Report (EIR), State Clearing House #2005061111. 

[CA PRC CEQA, 11-23-1970] 

[Devices subject to this condition 

0196] 

0159, 0165, 0171, 0177, 0183, 0189, 0195, 

El93.7 The operator shall operate and maintain this equipment according to the following 

requirements: 

The gas turbines shall operate with natural gas exclusively. 

The operator shall vent this equipment to the CO oxidation catalyst and SCR control 

system whenever the turbine is in operation. 

Written records of commissioning, startups, and shutdowns shall be maintained and 

made available upon request from AQMD. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 

1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002; RULE 1703 -PSD 

Analysis, 10-7-1988; RULE 2005, 5-6-2005] 

[Devices subject to this condition: 0159, 0165, 0171, DI 77, 0183, 0189] 

El93.9 The operator shall operate and maintain this equipment according to the following 

requirements: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 78 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall calculate and continuously record the NH3 slip concentration 

using the following equation 

NH3 (ppmvd) = [a-b*(c*l.2)/l,OOO,OOO]*l,000,000/b 

where a=NH3 injection rate (lb/hr)/l 7(1b/lb-mol), b= dry exhaust flow rate (scf/hr)/ 

(385.5 scf/lb-mol), c = change in measured NOx across the SCR, ppmvd at 15 

percent 02. 

The operator shall install a NOx analyzer to measure the SCR inlet NOx ppm accurate 

to within +/- 5 percent calibrated at least once every 12 months. The operator shall 

use the method described above or another alternative method approved by the 

Executive Officer. 

The ammonia slip calculation procedures described above shall not be used for 

compliance determination or emission information determination without 

corroborative data using an approved reference method for the determination of 

ammonia. The ammonia slip calculation procedure shall be in-effect no later than 90 

days after initial startup of the turbine. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] 

[Devices subject to this condition: Cl62, Cl68, Cl 74, Cl80, Cl86, Cl92] 

El93.IO The operator shall operate and maintain this equipment according to the following 

requirements: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D 

Facilitv ID: 

Revision#: 

Page: 79 

800074 

28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall not commence operation of any of the new Units 11-16 until the 

AQMD certifies that one of the following conditions has been satisfied: 

A, The facility has provided 292 lbs/day of federally enforceable PM2.5 emission 

reduction credits unless a different amount associated with the Repower Project 

modification at this facility as determined to be required according to the federal 

New Source Review (NSR) requirements (40CFR Part 51 Subpart Z Appendix S), as 

approved by both AQMD and EPA. 

B. The operator shall comply with a federally enforceable limit of JOO tons per year 

of PM2.5 emissions. 

For purposes of demonstrating compliance with the I 00 ton per year limit the 

operator shall determine the PM2.5 emissions for each of the major sources at the 

facility by calculating a 12-month rolling average using the following formula: 

PM2.5 = (FF! *EFI + FF2*EF2+ FF9*EF9+ FFIO*EFIO+ FFll*EFll+ 

FFl2*EF12+ FF13*EFl3+ FF14*EFl4+ FFl5*EFl5+ 

FFl6*EFl6+FFDI *EFDI +FFD2*EFD2)/2000 

Where: PM2.5 = PM2.5 emissions in tons per year, FFI= fuel flow for Unit I in 

MMscf, FF2= fuel flow for Unit 2 in MMscf, FF9= fuel flow for Unit 9 in MMscf, 

FFIO= fuel flow for Unit JO in MMscf, FFI I to FFl6= fuel flow for Units 11 to 16 

in MMscf, FFD I to FFD2 = diesel usage for two black start generator in Mgal. 

EF!= emission factor for Unit I= 7.14 lb/MMscf, EF2= emission factor for Unit 2 

6.61 lb/MMscf, EF9= em1ss1on factor for Unit 9 = l.238 lb/MMscf, EFIO= 

emission factor for Unit 10 = 0.968 lb/MMscf, EFI I to EF16 = emission factor for 

Units 11 to 16 = 6.423 lb/MMscf, EFD l to EFD2 = emission factor for two standby 

generators= 0.32 lb/Mgal. 

Any changes to these emission factors must be approved in advance by the District in 

writing and be based on unit specific source tests performed usmg a District 

approved testing protocol. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 80 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[40CFR Part 51, Appendix S, 10-20-2010] 

[Devices subject to this condition : Dl59, Dl65, 0171, Dl77, Dl83, 0189, D195, 

Dl96] 

E193.l l The operator shall operate and maintain this equipment according to the following 

requirements: 

a. CHANGE OIL AND FILTER EVERY 500 HOURS OF OPERATION OR 

ANNUALLY, WHICHEVER COMES FIRST. 

b. INSPECT 

ANNUALLY, 

AND 

AIR CLEANER EVERY 1,000 HOURS OF OPERATION OR 

WHICHEVER COMES FIRST, AND REPLACE AS NECESSARY; 

c. INSPECT ALL HOSES AND BEL TS EVERY 500 HOURS OF OPERATION OR 

ANNUALLY, WHICHEVER COMES FIRST, AND REPLACE AS NECESSARY. 

[40CFR 63 Subpart ZZZZ, 1-30-2013] 

[Devices subject to this condition : 053] 

E202. l The operator shall clean and maintain this equipment according to the following 

specifications: 

The operator shall wash and/or vacuum and then inspect the boiler ducts, stack, and air 

preheaters during each shutdown in which a boiler is cooled. The operator shall 

reinspect and perform additional cleaning on these areas as necessary prior to startup. 

The operator shall install and maintain a permanent stack washing system in the boiler 

stack 

The operator shall wash the stack prior to start-up each time the boiler is shut down 

for 48 hours or more 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D 

Facilltv ID· 

Revision#: 

Page: 81 

800074 

28 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

[RULE 401,3-2-1984; RULE 401, 11-9-2001] 

[Devices subject to this condition: DI, D4] 

E204.I The operator shall employ the fuel oil additive system according to the following 

specifications: 

The operator shall inject District-approved additives at a rate between 6,500 and 

10,500 parts of oil per part of additive, based on volume. 

The operator shall inject District-approved additives into the fuel oil whenever fuel 

oil is burned, as soon as fuel oil firing has stabilized. 

The operator shall take corrective action as expeditiously as practicable if there is a 

failure to comply with either of the above requirements, so that compliance is 

achieved within 48 hours of such failure; the operator shall switch the unit to natural 

gas fuel, provided such fuel is available, if such failure is longer than 48 hours, and 

will remain on natural gas until such time as the failure is corrected. 

The operator shall check the flow of fuel oil additive at least once a shift by 

recording the level of the additive in the holding tank. 

[RULE 401, 3-2-1984; RULE 401, 11-9-2001] 

[Devices subject to this condition : DI, D4] 

E204.2 The operator shall perform a boiler lancing according to the following specifications: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 82 

Facility ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall cycle the boiler and air preheater lancing continuously while 

burning fuel oil and shall commence as soon as oil firing has stabilized; the operator 

shall continue the lancing cycle for the first 24 hours following a change from fuel 

oil to natural gas. 

The operator shall cycle the air preheater lances and boiler lances once daily and 

once weekly, respectively, during periods of natural gas burning. 

The operator shall repair and return to services individual lances as soon as 

practicable; the operator shall switch the unit to natural gas, provided such fuel is 

available, in the event that five or more lances are out of service simultaneously for 

more than 48 hours, and shall keep the unit on natural gas until such time as the 

repairs have been completed so that no more than two lances remain out of service. 

[RULE 401, 3-2-1984; RULE 401, 11-9-2001) 

[Devices subject to this condition : DI, 04) 

E448. I The operator shall comply with the following requirements: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 83 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The engine and the Johnson Matthey CRT+ diesel particulate filter shall be operated 

in accordance with CARB Executive Order DE-08-009-04. 

The engine shall operate at the load level required to achieve 240 0C for a mmtmum 

of 40% of the engine's operating time and a NOx/PM ratio of 15 @ >= 300 0C and 

20 @ <= 300 0C. The NOx/PM ratio shall be at least 8 with a preference for 20 or 

higher. 

The engine shall not operate below passive regeneration temperature for more than 

720 consecutive minutes. Regeneration is required after 24 consecutive cold starts 

and 30-minute idle sessions. 

Filter cleaning is required after 150 half-hour cold starts with associated 

regeneration or 1000 hours of emergency use. The CRTdm, which monitors engine 

exhaust back pressure and temperature will determine the actual cleaning interval and 

provide an alert when filter cleaning is required. 

The operator shall keep records of any corrective action taken after the CRTdm has 

notified the operator that a high pressure limit is reached. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1470, 

5-4-2012] 

[Devices subject to this condition : D 195, D 196] 

E448.2 The operator shall comply with the following requirements: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar. CA 91765-41 78 

Section D 

Facilitv ID: 

Page: 84 

800074 

Revision#: 28 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Removal of the diesel particulate filter's filter media for cleaning may only occur 

under the following conditions: 

A. The internal combustion engine shall not be operated for maintenance and testing 

or any other non-emergency use while the diesel particulate filter media is removed; 

and 

B. The diesel particulate filter's filter media shall be returned and re-installed within 

10 working days from the date of removal; and 

C. The owner or operator shall maintain records indicating the date(s) the diesel 

particulate filter's filter media was removed for cleaning and the date(s) the filter 

media was re-installed. Records shall be retained for a minimum period of 36 

months. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1470, 

5-4-2012] 

[Devices subject to this condition : D 195, D 196] 

E448.3 The operator shall comply with the following requirements: 

The engine shall comply with the emission standards specified in 40 CFR 60.4204(b) 

and 4205(b ). The operator must comply by purchasing an engine certified to the 

emission standards in 40 CFR 60.4204(b), or 4205(b) or (c), as applicable, for the 

model year and maximum engine power. The engine must be installed and configured 

according to the manufacturer's specifications. 

The engine and the control device shall be operated and maintained in accordance 

with the manufacturer's written emission-related instructions or procedures 

developed by the operator that are approved by the engine manufacturer. Changes to 

those emission-related settings that are set by the manufacturer are not allowed. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Section D Page: 85 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14. 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall com ply with the terms and conditions set forth below: 

[40CFR 60 Subpart IITI, 7-11-2006] 

[Devices subject to this condition : D l 9S, D 196] 

H. Applicable Rules 

H23.l This equipment is subject to the applicable requirements of the following rules or 

regulations: 

Contaminant Rule Rule/Subpart 

voe District Rule 463 

[RULE 463, 3-11-1994] 

[Devices subject to this condition: D46, D47, D48, D49, DSO] 

H23.3 This equipment is subject to the applicable requirements of the following rules or 

regulations: 

Contaminant Rule Rule/Subpart 

voe District Rule 464 

[RULE 464, 12-7-1990] 

[Devices subject to this condition : Dll6, Dll7, Dll8, Dll9, Dl20, 0122, Dl23, 

DIS4, DISS] 

H23.S This equipment is subject to the applicable requirements of the following rules or 

regulations: 

Contaminant Rule Rule/Subpart 
South Coast Air Quality Management District 

Z 1865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 86 

Facilitv ID: 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRJPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Refrigerants I District Rule I 1415 

[RULE 1415, 10-14-1994] 

[Devices subject to this condition : E 113] 

H23.6 This equipment is subject to the applicable requirements of the following rules or 

regulations: 

Contaminant 

Refrigerants 

Refrigerants 

Rule 

40CFR82, SUBPART 

District Rule 

Rule/Subpart 

B 

1411 

[RULE 1411, 3-1-1991; 40CFR 82 Subpart B, 7-14-1992] 

[Devices subject to this condition : E 114] 

K. Record Keeping/Reporting 

K40.3 The operator shall provide to the District a source test report in accordance with the 

following specifications: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar. CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 87 

Facility ID· 800074 

Revision#: 28 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Source test results shall be submitted to the District no later than 60 days after the 

source test was conducted. 

Emission data shall be expressed in terms of concentration (ppmv), corrected to 15 

percent oxygen, dry basis. 

All exhaust flow rate shall be expressed in terms of dry standard cubic feet per 

minute (DSCFM) and dry actual cubic feet per minute (DACFM). 

All moisture concentration shall be expressed in terms of percent corrected to 15 

percent oxygen. 

Emission data shall be expressed in terms of mass rate (lbs/hr). In addition, solid 

PM emissions, if required to be tested, shall also be reported in terms of grains per 

DSCF. 

Source test results shall also include fuel flow and exhaust gas rate under which the 

test was conducted. 

Source test results shall also include turbine and generator output under which the 

test was conducted. 

Emission data shall be expressed in terms of lbs/MM cubic feet. 

[RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 

1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002; RULE 2005, 

4-9-1999; RULE 2005, 4-20-2001] 

[Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] 

K67.l The operator shall keep records, in a manner approved by the District, for the following 

parameter(s) or item(s): 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section D Page: 88 

Facility JD· 800074 

Revision#: 28 

Date· January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

the name of the person perfonning the inspection and/or maintenance of the dust 

collector 

the date, time and results of the inspection 

the date, time and description of any maintenance or repairs resulting from the 

inspection 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition : E 112] 

K67 .2 The operator shall keep records, in a manner approved by the District, for the following 

parameter(s) or item(s): 

The operator shall monitor and record on a daily basis the flowrate of the incoming 

scrubbing (city) water when this scrubber is operated 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition : C40, C4 l] 

K67.3 The operator shall keep records, in a manner approved by the District, for the following 

parameter(s) or item(s): 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D 

Facilitv ID: 

Page: 89 

800074 

Revision#: 28 

Date: January 14,2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

For architectural applications where no thinners, reducers, or other VOC containing 

materials are added, maintain semi-annual records for all coating consisting of (a) 

coating type, (b) voe content as supplied in grams per liter (g/l) of materials for 

low-solids coatings, (c) voe content as supplied in g/I of coating, less water and 

exempt solvent, for other coatings. 

For architectural applications where thinners, reducers, or other VOC containing 

materials are added, maintain daily records for each coating consisting of (a) coating 

type, (b) voe content as applied in grams per liter (g/l) of materials used for 

low-solids coatings, (c) voe content as applied in g/I of coating, less water and 

exempt solvent, for other coatings. 

[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic 

Monitoring, 12-12-1997] 

[Devices subject to this condition : E 124] 

K67.4 The operator shall keep records, in a manner approved by the District., for the following 

parameter(s) or item(s): 

Natural gas and Diesel fuel usage after eEMS certification. 

The date, time, duration, and CEMS minute data for start-ups. These records shall be 

maintained and made available upon request from AQMD 

[RULE 2012, 5-6-2005] 

[Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] 

K67.5 The operator shall keep records, in a manner approved by the District, for the following 

parameter(s) or item(s): 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D 

Facility ID· 

Revision#: 

Page: 90 

800074 

28 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

Date of operation, the elapsed time, in hours, and the reason for operation. Records 

shall be kept and maintained on file for a minimum of two years and made available to 

district personnel upon request. 

An engine operating log listing on a monthly basis the emergency use hours of 

operation, maintenance and testing hours of operation, and any other hours of use 

with a description of the reason for operation. Additionally, each time the engine is 

started manually, the log shall include the date of operation and the timer reading in 

hours at the beginning and end of operation. 

The log shall be kept for a minimum of three calendar years prior to the current year 

and be made available to District personnel upon request. The total hours of operation 

for the previous calendar year shall be recorded sometime during the first 15 days of 

January of each year. 

[RULE 1110.2, 2-1-2008; RULE 1304(a)-Modeling and Offset Exemption, 6-14-1996; 

RULE 14 70, 6-1-2007] 

[Devices subject to this condition : D53] 

K67.6 The operator shall keep records, in a manner approved by the District, for the following 

parameter(s) or item(s): 

Natural gas fuel use during the commissioning period 

[RULE 2012, 5-6-2005] 

[Devices subject to this condition: D159, Dl65, DI 71, DI 77, D183, DI 89] 

K67.7 The operator shall keep records, in a manner approved by the District, for the following 

parameter(s) or item(s): 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section D 

Facilitv ID: 

Page: 91 

800074 

Revision#: 28 

Date: January14.2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS 

The operator shall comply with the terms and conditions set forth below: 

The operator shall keep a log of engine operations documenting the total time the 

engine is operated each month and the specific reason for operation as: A) 

Emergency Use, B) Maintenance and Testing, or C) Other (be specific) 

In addition, for each time the engine is manually started, the log shall include the date 

of engine operation, the specific reason for operation, and the totalizing hour meter 

reading (in hours and tenths of hours) at the beginning and the end of the operation. 

On or before January 15th of each year the operator shall record in the engine 

operating log: A) the total hours of engine operation for the previous calendar year, 

and B) the total hours of engine operation for maintenance and testing for the 

previous calendar year. 

Records shall be kept and maintained on file for a mm1mum of five years and made 

available to district personnel upon request. 

[RULE 1304(c)-Offset Exemption, 6-14-1996; RULE 1470, 5-4-2012; RULE 3004(a)(4) 

-Periodic Monitoring, 12-12-1997; 40CFR 60 Subpart Illl, 7-11-2006] 

[Devices subject to this condition: Dl95, Dl96] 

Kl 71.1 The operator shall notify the District if any of the following situations occur: 

When fuel oil is fired in this equipment 

This notification shall be provided to the District no later than 48 hours after fuel oil 

is fired in this boiler. 

[RULE 401, 3-2-1984; RULE 401, 11-9-2001] 

[Devices subject to this condition: DI, 04] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-4178 

FACILITY PERMIT TO OPERATE 

Section E Page: I 

Facilitv ID: 800074 

Revision#· 16 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION E: ADMINISTRATIVE CONDITIONS 

The operating conditions in this section shall apply to all permitted equipment at this 

facility unless superseded by condition(s) listed elsewhere in this permit. 

I. The permit shall remain effective unless this permit is suspended, revoked, 

modified, reissued, denied, or it is expired for nonpayment of permit processing or 

annual operating fees. [201, 203, 209, 301] 

a. The permit must be renewed annually by paying annual operating fees, and the 

permit shall expire if annual operating fees are not paid pursuant to 

requirements of Rule 30l(d). [30l(d)] 

b. The Permit to Construct listed in Section H shall expire one year from the 

Permit to Construct issuance date, unless a Permit to Construct extension has 

been granted by the Executive Officer or unless the equipment has been 

constructed and the operator has notified the Executive Officer prior to the 

operation of the equipment, in which case the Permit to Construct serves as a 

temporary Permit to Operate. [202, 205] 

c. The Title V permit shall expire as specified under Section K of the Title V 

permit. The permit expiration date of the Title V facility permit does not 

supercede the requirements of Rule 205. [205, 3004] 

2. The operator shall maintain all equipment in such a manner that ensures proper 

operation of the equipment. [204] 

3. This permit does not authorize the emissions of air contaminants in excess of those 

allowed by Division 26 of the Health and Safety Code of the State of California or 

the Rules and Regulations of the SCAQMD. This permit cannot be considered as 

permission to violate existing laws, ordinances, regulations, or statutes of other 

governmental agencies. [204] 

4. The operator shall not use equipment identified in this facility permit as being 

connected to air pollution control equipment unless they are so vented to the 

identified air pollution control equipment which is in full use and which has been 

included in this permit. [204] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section E Page: 2 

Facilitv ID: 800074 

Revision#: 16 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION E: ADMINISTRATIVE CONDITIONS 

5. The operator shall not use any equipment having air pollution control device( s) 

incorporated within the equipment unless the air pollution control device is in full 

operation. [204] 

6. The operator shall maintain records to demonstrate compliance with rules or permit 

conditions that limit equipment operating parameters, or the type or quantity of 

material processed. These records shall be made available to SCAQMD personnel 

upon request and be maintained for at least: [204] 

a. Three years for a facility not subject to Title V; or 

b. Five years for a facility subject to Title V. 

7. The operator shall maintain and operate all equipment to ensure compliance with 

all emission limits as specified in this facility permit. Compliance with emission 

limits shall be determined according to the following specifications, unless 

otherwise specified by SCAQMD rules or permit conditions: [204] 

a. For internal combustion engines and gas turbines, measured concentrations shall 

be corrected to 15 percent stack-gas oxygen content on a dry basis and be 

averaged over a period of 15 consecutive minutes; [1110.2, 1134, 204] 

b. For other combustion devices, measured concentrations shall be corrected to 3 

percent stack-gas oxygen content on a dry basis and be averaged over a period 

of 15 consecutive minutes; [1146, 1146.1, 204] 

c. For a large NOx source, compliance with a RECLAIM concentration limit shall 

be measured over a continuous 60 minutes for that source; [2012] 

d. For non-combustion sources, compliance with emission limits shall be 

determined and averaged over a period of 60 minutes; [204] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar. CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section E Page: 3 

Facility ID: 800074 

Revision#: 16 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION E: ADMINISTRATIVE CONDITIONS 

e. For the purpose of determining compliance with Rule 407, carbon monoxide 

(CO) shall be measured on a dry basis and be averaged over IS consecutive 

minutes, and sulfur compounds which would exist as liquid or gas at standard 

conditions shall be calculated as sulfur dioxide (S02) and be averaged over IS 

consecutive minutes; [ 407] 

f. For the purpose of determining compliance with Rule 409, combustion 

contaminant emission measurements shall be corrected to 12 percent of carbon 

dioxide (C02) at standard conditions and averaged over IS consecutive 

minutes. [ 409] 

g. For the purpose of determining compliance with Rule 475, combustion 

contaminant emission measurements shall be corrected to 3 percent of oxygen 

(02) at standard conditions and averaged over IS consecutive minutes or any 

other averaging time specified by the Executive Officer. [475] 

8. All equipment operating under the RECLAIM program shall comply concurrently 

with all SCAQMD Rules and Regulations, except those listed in Table I of Rule 

2001 for NOx RECLAIM sources and Table 2 of Rule 2001 for SOx RECLAIM 

sources. Those provisions listed in Tables 1 or 2 shall not apply to NOx or SOx 

emissions after the date the facility has demonstrated compliance with all 

monitoring and reporting requirements of Rules 2011 or 2012, as applicable. 

Provisions of the listed SCAQMD rules in Tables 1 or 2 which have initial 

implementation dates in 1994 shall not apply to a RECLAIM NOx or SOx source, 

respectively. [200 l] 

9. The operator shall, when a source test is required by SCAQMD, provide a source 

test protocol to SCAQMD no later than 60 days before the proposed test date. The 

test shall not commence until the protocol is approved by SCAQMD. The test 

protocol shall contain the following information: [204, 304] 

a. Brief description of the equipment tested. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section E Page: 4 

Facilitv ID: 800074 

Revision#: 16 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION E: ADMINISTRATIVE CONDITIONS 

b. Brief process description, including maximum and normal operating 

temperatures, pressures, through-put, etc. 

c. Operating conditions under which the test will be performed. 

d. Method of measuring operating parameters, such as fuel rate and process 

weight. Process schematic diagram showing the ports and sampling locations, 

including the dimensions of the ducts/stacks at the sampling locations, and 

distances of flow disturbances, ( e,g. elbows, tees, fans, dampers) from the 

sampling locations (upstream and downstream). 

e. Brief description of .sampling and analytical methods used to measure each 

pollutant, temperature, flow rates, and moisture. 

£ Description of calibration and quality assurance procedures. 

g. Determination that the testing laboratory qualifies as an "independent testing 

laboratory" under Rule 304 (no conflict of interest). 

l O. The operator shall submit a report no later than 60 days after conducting a source 

test, unless otherwise required by SCAQMD Rules or equipment-specific 

conditions. The report shall contain the following information: [204] 

a. The results of the source test. 

b. Brief description of the equipment tested. 

c. Operating conditions under which test will be performed. 

d. Method of measuring operating parameters, such as fuel rate and process 

weight. Process schematic diagram showing the ports and sampling locations, 

including the dimensions of the ducts/stacks at the sampling locations, and 

distances of flow disturbances, (e.g. elbows, tees, fans, dampers) from the 

sampling locations (upstream and downstream). 

e. Field and laboratory data forms, strip charts and analyses. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section E Page: 5 

Facilitv ID: 800074 

Revision#: 16 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION E: ADMINISTRATIVE CONDITIONS 

f. Calculations for volumetric flow rates, emission rates, control efficiency, and 

overall control efficiency. 

11. The operator shall, when a source test is required, provide and maintain facilities 

for sampling and testing. These facilities shall comply with the requirements of 

SCAQMD Source Test Method I.I and 1.2. [217] 

12. Whenever required to submit a written report, notification or other submittal to the 

Executive Officer, SCAQMD, or the District, the operator shall mail or deliver the 

material to: Deputy Executive Officer, Engineering and Compliance, SCAQMD, 

21865 E. Copley Drive, Diamond Bar, CA 91765-4182. [204] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section F Page: I 

Facilitv ID: 800074 

Revision#: 12 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION F: RECLAIM MONITORING AND SOURCE TESTING REQUIREMENTS 

The Facility shall comply with all applicable monitoring and source testing requirements in 

Regulation XX. These requirements may include but are not limited to the following: 

I. NOx Monitoring Conditions 

A. The Operator of a NOx Major Source, as defined in Rule 2012, shall, as applicable: 

I. Install, maintain, and operate an SCAQMD certified direct or time-shared 

monitoring device or an approved alternative monitoring device for each major 

NOx source to continuously measure the concentration ofNOx emissions and all 

other applicable variables specified in Rule 2012, Table 2012-1 and Rule 2012, 

Appendix A, Table 2-A to determine the NOx emissions rate from each source. 

The time-sharing ofCEMS among NOx sources may be allowed by the Executive 

Officer in accordance with the requirements for time sharing specified in Appendix 

A. [2012] 

2. Install, maintain, and operate a totalizing fuel meter approved by the Executive 

Officer for each major source. [2012] 

3. If the facility is operating existing CEMS and fuel meters, continue to follow 

recording and reporting procedures required by SCAQMD Rules and Regulations 

in effect prior to October 15, 1993 until the CEMS is certified pursuant to Rule 

2012. [2012] 

4. Use valid data collected by an SCAQMD certified or provisionally certified CEMS 

in proper operation that meets all the requirements of Appendix A of Rule 2012, 

unless final certification of the CEMS is denied, to determine mass emissions for 

all purposes, including, but not limited to, determining: [2012] 

a. compliance with the annual Allocation; 

b. excess emissions; 

c. the amount of penalties; and 

d. fees. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

FACILITY PERMIT TO OPERATE 

Section F Page· 2 

Facilitv ID: 800074 

Revision#: 12 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION F: RECLAIM MONITORING AND SOURCE TESTING REQUIREMENTS 

5. Follow missing data procedures as specified in Rule 2012 Appendix A whenever 

valid data is not available or collected to determine mass emissions for all 

purposes, including, but not limited to, determining: (2012] 

a. compliance with the annual Allocation; 

b. excess emissions; 

c. the amount of penalties; and 

d. fees. 

B. The Operator of a NOx Large Source, as defined in Rule 2012, shall, as applicable: 

Not Applicable 

C. The Operator ofa NOx Process Unit, as defined in Rule 2012, shall, as applicable: 

I. Install, maintain, and operate a totalizing fuel meter or any device approved by the 

Executive Officer to measure quarterly fuel usage or other applicable variables 

specified in Rule 2012, Table 2012-1, and Rule 2012, Appendix A, Table 4-A. 

The sharing of totalizing fuel meters may be allowed by the Executive Officer if 

the fuel meter serves process units which have the same emission factor or 

emission rate. The sharing of totalizing meter shall not be allowed for process units 

which are required to comply with an annual heat input limit. (2012] 

II. NOx Source Testing and Tune-up conditions 

I. The operator shall conduct all required NOx source testing in compliance with an 

SCAQMD-approved source test protocol. (2012] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section F Page: 3 

Facilitv ID: 800074 

Revision#: 12 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION F: RECLAIM MONITORING AND SOURCE TESTING REQUIREMENTS 

2. The operator shall, as applicable, conduct source tests for every large NOx source 

no later than December 31, 1996 and every 3 years thereafter. The source test 

shall include the determination ofNOx concentration and a relative accuracy audit 

of the exhaust stack flow determination (e.g. in-stack flow monitor or fuel flow 

monitor based F-factor calculation). Such source test results shall be submitted per 

the schedule described by APEP. Jn lieu of submitting the first source test report, 

the facility permit holder may submit the results of a source test not more than 3 

years old which meets the requirements when conducted. [2012] 

3. All NOx large sources and NOx process units shall be tuned-up in accordance with 

the schedule specified in Rule 2012, Appendix A, Chapter 5, Table 5-B. [2012] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section G Page: I 

Facilitv ID: 800074 

Revision#: 13 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION G: RECORDKEEPING AND REPORTING REQUIREMENTS FOR 

RECLAIM SOURCES 

The Facility shall comply with all applicable reporting and recordkeeping requirements in 

Regulation XX. These requirements may include but are not limited to the following: 

I. Recordkeeping Requirements for all RECLAIM Sources 

I . The operator shall maintain all monitoring data required to be measured or reported 

pursuant to Rule 2011 and Rule 2012, whichever is applicable. All records shall be 

made available to SCAQMD staff upon request and be maintained for at least: 

a. Three years after each APEP report is submitted to SCAQMD for a facility 

not subject to Title V, unless a different time period is required in Rule 2011 

or Rule 2012 [2011 & 2012]; or 

b. Five years after each APEP report is submitted to SCAQMD for a facility 

subject to Title V. [3004(a)(4)(E)] 

c. Notwithstanding the above, all data gathered or computed for intervals of 

less than 15 minutes shall only be maintained a minimum of 48 hours. [2011 

& 2012] 

2. The operator shall store on site and make available to the Executive Officer upon 

request: records used to determine emissions, maintenance records, sources test 

reports, relative accuracy test audit reports, relative accuracy audit reports and fuel 

meter calibration records. [2011 & 2012] 

II. Reporting Requirements for all RECLAIM Sources 

I. The opearator shall submit a quarterly certification of emissions including the total 

facility NOx or SOx emissions, whichever is applicable, for the quarter within 30 

days after the end of the first three quarters and 60 days after the end of the fourth 

quarter of a compliance year. [2004] 

NOx Reporting Requirements 

A. The Operator of a NOx Major Source, as defined in Rule 2012, shall, as applicable: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section G Page: 2 

Facilitv ID: 800074 

Revision#: 13 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION G: RECORDKEEPING AND REPORTING REQUIREMENTS FOR 

RECLAIM SOURCES 

1. No later than 12 months after entry into the RECLAIM program or after the initial 

operation of a new major source, whichever is later, install, maintain, and operate a 

reporting device to electronically report everyday to the SCAQMD central station 

for each major NOx source, the total daily mass emissions ofNOx and daily status 

codes. Such data shall be transmitted by 5:00 p.m. of the following day. If the 

facility experiences a power, computer, or other system failure that prevents the 

submittal of the daily report, the Facility Permit holder shall be granted 24 hours 

extension to submit the report. [2012) 

2. Calculate NOx emissions pursuant to missing data procedures set forth in Appendix 

A, Chapter 2 of Rule 2012 ifthe Facility Permit holder fails to meet the deadline 

for submitting the daily report. Notwithstanding the preceding condition, in no 

more than three non-consecutive occurrences per compliance year the reporting 

deadline extension following a system failure that precludes the Facility Permit 

holder from timely reporting shall be 96 rather than 24 hours provided that the raw 

data as obtained by the direct monitoring device is stored at the facility. [2012] 

3. Submit an electronic report within 15 days following the end of each month totaling 

NOX emissions from all major NOx sources during the month. [2012] 

4. For those facilities with existing CEMS and fuel meters as of October 15, 1993, 

continue to follow recording and reporting procedures required by SCAQMD Rules 

and Regulations in effect until the CEMS is certified pursuant to Rule 2011 and/or 

Rule 2012, as applicable. [2012] 

B. The Operator of a NOx Large Source, as defined in Rule 2012, shall: 

Not Applicable 

C. The Operator ofa NOx Process Unit, as defined in Rule 2012, shall: 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-4178 

FACILITY PERMIT TO OPERATE 

Section G Page: 3 

Facilitv ID: 800074 

Revision#: 13 

Date· January 14,2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION G: RECORDKEEPING AND REPORTING REQUIREMENTS FOR 

RECLAIM SOURCES 

1. Electronically report the calculated quarterly NOx emissions for each NOx process 

unit. The Operator shall comply with this requirement within 12 months of the 

date of entry to the RECLAIM Program. [2012] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section H Page: I 

Facility ID: 800074 

Revision#: 30 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION H: PERMIT TO CONSTRUCT AND TEMPORARY PERMIT TO OPERA TE 

NONE 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION I: PLANS AND SCHEDULES 

Section I Page· I 

Facilitv JD· 800074 

Revision#: 10 

Date: January 14, 2015 

This section lists all plans approved by AQMD for the purposes of meeting the requirements of applicable 

AQMDrules. 

NONE 

NOTE: This section does not list compliance schedules pursuant to the requirements of Regulation XXX - Title 

V Permits; Rule 3004(a)(IO)(C). For equipment subject to a variance, order for abatement, or alternative 

operating condition granted pursuant to Rule 518.2, equipment specific conditions are added to the equipment in 

Section D or H of the permit. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section J Page: I 

Facility ID: 800074 

Revision#: 7 

Date: January 14. 2015 

LA CITY, DWP BAYNES GENERATING STATION 

SECTION J: AIR TOXICS 

NOT APPLICABLE 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page: I 

Facility ID: 800074 

Revision#: 8 

Date· January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

GENERAL PROVISIONS 

1. This pennit may be revised, revoked, reopened and reissued, or tenninated for cause, or 

for failure to comply with regulatory requirements, pennit tenns, or conditions. 

[3004(a)(7)(C)] 

2. This pennit does not convey any property rights of any sort or any exclusive privilege. 

[3004(a)(7)(E)] 

Permit Renewal and Expiration 

3. (A) Except for solid waste mcmeration facilities subject to standards under 

section 129(e) of the Clean Air Act, this pennit shall expire five years from the 

date that this Title V pennit is issued. The operator's right to operate under this 

pennit tenninates at midnight on this date, unless the facility is protected by an 

application shield in accordance with Rule 3 002(b ), due to the filing of a timely 

and complete application for a Title V pennit renewal, consistent with Rule 3003. 

[3004(a)(2), 3004(t)] 

(B) A Title V pennit for a solid waste incineration facility combusting municipal 

waste subject to standards under Section 129( e) of the Clean Air Act shall expire 

12 years from the date of issuance unless such pennit has been renewed pursuant 

to this regulation. These pennits shall be reviewed by the Executive Officer at 

least every five years from the date of issuance. [3004(t)(2)] 

4. To renew this pennit, the operator shall submit to the Executive Officer an application for 

renewal at least J 80 days, but not more than 545 days, prior to the expiration date of this 

pennit. [3003(a)(6)] 

Duty to Provide Information 

5. The applicant for, or holder of, a Title V pennit shall furnish, pursuant to Rule 3002(d) 

and ( e ), timely infonnation and records to the Executive Officer or designee within a 

reasonable time as specified in writing by the Executive Officer or designee. 

[3004(a)(7)(F)] 

Payment of Fees 

6. The operator shall pay all required fees specified in Regulation Ill - Fees. [3004(a)(7)(G)] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page: 2 

Fac:ilitv ID: 800074 

Revision#' 8 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

Reopening for Cause 

7. The Executive Officer will reopen and revise this permit if any of the following 

circumstances occur: 

(A) Additional regulatory requirements become applicable with a remaining permit 

term of three or more years. Reopening is not required if the effective date of the 

requirement is later than the expiration date of this permit, unless the permit or 

any of its terms and conditions has been extended pursuant to paragraph (f)(4) of 

Rule 3004. 

(B) The Executive Officer or EPA Administrator determines that this permit contains 

a material mistake or that inaccurate statements were made in establishing the 

emissions standards or other terms or conditions of this permit. 

(C) The Executive Officer or EPA Administrator determines that the permit must be 

revised or revoked to assure compliance with the applicable requirements. 

[3005(g)(l )] 

COMPLIANCE PROVISIONS 

8. The operator. shall comply with all regulatory requirements, and all permit terms and 

conditions, except: 

(A) As provided for by the emergency provisions of condition no. 17 or condition no. 

18, or 

(B) As provided by an alternative operating condition granted pursuant to a federally 

approved (SIP-approved) Rule 518.2. 

Any non-compliance with any federally enforceable permit condition constitutes a 

violation of the Federal Clean Air Act and is grounds for enforcement action; for 

permit termination, revocation and reissuance, or revision; or denial of a permit 

renewal application. Non-compliance may also be grounds for civil or criminal 

penalties under the California State Health and Safety Code. (3004(a)(7)(A)] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page· 3 

Facility ID: 800074 

Revision #: 8 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

9. The operator shall allow the Executive Officer or authorized representative, upon 

presentation of appropriate credentials to: 

(A) Enter the operator's premises where emission-related activities are conducted, or 

records are kept under the conditions of this permit; 

(B) Have access to and copy, at reasonable times, any records that must be kept under 

the conditions of the permit; 

(C) Inspect at reasonable times, any facilities, equipment (including monitoring and 

air pollution control equipment), practices, or operations regulated or required 

under the permit; and 

(D) Sample or monitor at reasonable times, substances or parameters for the purpose 

of assuring compliance with the facility permit or regulatory requirements. 

[3004(a)(l O)(B)] 

10. All terms and conditions in this permit, including any provisions designed to limit a 

facility's potential to emit, are enforceable by the EPA Administrator and citizens under 

the federal Clean Air Act, unless the term or condition is designated as not federally 

enforceable. Each day during any portion of which a violation occurs is a separate 

offense. [3004(g)) 

11. A challenge to any permit condition or requirement raised by EPA, the operator, or any 

other person, shall not invalidate or otherwise affect the remaining portions of this 

permit. [3007(b )) 

12. The filing of any application for a permit revision, revocation, or termination, or a 

notification of planned changes or anticipated non-compliance does not stay any permit 

condition. [3004(a)(7)(D)] 

13. It shall not be a defense for a person in an enforcement action, including those listed in 

Rule 3002(c)(2), that it would have been necessary to halt or reduce the permitted activity 

in order to maintain compliance with the conditions of this permit, except as provided for 

in "Emergency Provisions" of this section. [3004(a)(7)(H)] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page: 4 

Facilitv ID 800074 

Revision#: 8 

Date: January 14. 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

14. The operator shall not build, erect, install, or use any equipment, the use of which, 

without resulting in a reduction in the total release of air contaminants to atmosphere, 

reduces or conceals an emission which would otherwise constitute a violation of Chapter 

3 (commencing with Section 41700) of Part 4, of Division 26 of the California Health 

and Safety Code or of AQMD rules. This rule shall not apply to cases in which the only 

violation involved is of Section 41700 of the California Health and Safety Code, or Rule 

402 of AQMD Rules. (408] 

15. Nothing in this permit or in any permit shield can alter or affect: 

(A) Under Section 303 of the federal Clean Air Act, the provisions for emergency 

orders; 

(B) The liability of the operator for any violation of applicable requirements prior to 

or at the time of permit issuance; 

(C) The applicable requirements of the Acid Rain Program, Regulation XXXI; 

(D) The ability of EPA to obtain information from the operator pursuant to 

Section 114 of the federal Clean Air Act; 

(E) The applicability of state or local requirements that are not "applicable 

requirements'', as defined in Rule 3000, at the time of permit issuance but which 

do apply to the facility, such as toxics requirements unique to the State; and 

(F) The applicability of regulatory requirements with compliance dates after the 

permit issuance date. [3004(c)(3)] 

16. For any portable equipment that requires an AQMD or state permit or registration, 

excluding a) portable engines, b) military tactical support equipment and c) AQMDpermitted portable equipment that are not a major source, are not located at the facility 

for more than 12 consecutive months after commencing operation, and whose operation 

does not conflict with the terms or conditions of this Title V permit: 1) the facility 

operator shall keep a copy of the AQMD or state permit or registration; 2) the equipment 

operator shall comply with the conditions on the permit or registration and all other 

regulatory requirements; and 3) the facility operator shall treat the permit or registration 

as a part of its Title V permit, subject to recordkeeping, reporting and certification 

requirements. [3004(a)(l )] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

FACILITY PERMIT TO OPERATE 

Section K Page: 5 

Facility ID: 800074 

Revision#: 8 

Date: January 14, 2015 

LA CITY, DWP HA YNES GENERATING STATION 

SECTION K: TITLE V Administration 

EMERGENCY PROVISIONS 

17. An emergency' constitutes an affirmative defense to an action brought for noncompliance 

with a technology-based emission limit only if: 

(A) Properly signed, contemporaneous operating records or other credible evidence 

demonstrate that: 

(1) An emergency occurred and the operator can identify the cause(s) of the 

emergency; 

(2) The facility was operated properly (i.e. operated and maintained in 

accordance with the manufacturer's specifications, and in compliance with 

all regulatory requirements or a compliance plan), before the emergency 

occurred; 

(3) The operator took all reasonable steps to minimize levels of emissions that 

exceeded emissions standard, or other requirements in the permit; and, 

(4) The operator submitted a written notice of the emergency to the AQMD 

within two working days of the time when the emissions limitations were 

exceeded due to the emergency. The notice shall contain a description of 

the emergency, any steps taken to mitigate emissions, and corrective 

actions taken; and 

(B) The operator complies with the breakdown provisions of Rule 430 - Breakdown 

Provisions, or subdivision (i) of Rule 2004 - Requirements, whichever is 

applicable. [3002(g), 430, 2004(i)] 

18. The operator is excused from complying with any regulatory requirement that is 

suspended by the Executive Officer during a state of emergency or state of war 

emergency, in accordance with Rule 118 - Emergencies. [118] 

1 "Emergency" means any situation arising from sudden and reasonably unforeseeable events 

beyond the control of the operator, including acts of God, which: (A) requires immediate 

corrective action to restore normal operation; and (B) causes the facility to exceed a technologybased emission limitation under the permit, due to unavoidable increases in emissions attributable 

to the emergency; and (C) is not caused by improperly designed equipment, lack of preventative 

maintenance, careless or improper operation, or operator error. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page: 6 

Facilitv ID: 800074 

Revision#: 8 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

RECORD KEEPING PROVISIONS 

19. In addition to any other recordkeeping requirements specified elsewhere in this permit, 

the operator shall keep records ofrequired monitoring information, where applicable, that 

include: 

(A) The date, place as defined in the Title V permit, and time of sampling or 

measurements; 

(B) The date(s) analyses were performed; 

(C) Tlie company or entity that performed the analyses; 

(D) The analytical techniques or methods used; 

(E) The results of such analyses; and 

(F) The operating conditions as existing at the time of sampling or measurement. 

[3004(a)(4)(B)] 

20. The operator shall maintain records pursuant to Rule I 09 and any applicable material 

safety data sheet (MSDS) for any equipment claimed to be exempt from a written permit 

by Rule 219 based on the information in those records. [2! 9(t)] 

21. The operator shall keep all records of monitoring data required by this permit or by 

regulatory requirements for a period of at least five years from the date of the monitoring 

sample, measurement, report, or application. [3004(a)(4)(E)] 

REPORTING PROVISIONS 

22. The operator shall comply with the following requirements for prompt reporting of 

deviations: 

(A) Breakdowns shall be reported as required by Rule 430 - Breakdown Provisions or 

subdivision (i) of Rule 2004 - Requirements, whichever is applicable. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page: 7 

Facilitv ID: 800074 

Revision#· 8 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

(B) Other deviations from permit or applicable rule emission limitations, equipment 

operating conditions, or work practice standards, determined by observation or by 

any monitoring or testing required by the permit or applicable rules that result in 

emissions greater than those allowed by the permit or applicable rules shall be 

reported within 72 hours (unless a shorter reporting period is specified in an 

applicable State or Federal Regulation) of discovery of the deviation by 

contacting AQMD enforcement personnel assigned to this facility or otherwise 

calling (800) CUT-SMOG. 

(C) A written report of such deviations reported pursuant to (B), and any corrective 

actions or preventative measures taken, shall be submitted to AQMD, m an 

AQMD approved format, within 14 days of discovery of the deviation. 

(D) All other deviations shall be reported with the monitoring report required by 

condition no. 23. [3004(a)(5)] 

23. Unless more frequent reporting of monitoring results are specified in other permit 

conditions or in regulatory requirements, the operator shall submit reports of any required 

monitoring to the AQMD at least twice per year. The report shall include a) a statement 

whether all monitoring required by the permit was conducted; and b) identification of all 

instances of deviations from permit or regulatory requirements. A report for the first six 

calendar months of the year is due by August 31 and a report for the last six calendar 

months of the year is due by February 28. [3004(a)(4)(F)] 

24. The operator shall submit to the Executive Officer and to the Environmental Protection 

Agency (EPA), an annual compliance certification. For RECLAIM facilities, the 

certification is due when the Annual Permit Emissions Program (APEP) report is due and 

shall cover the same reporting period. For other facilities, the certification is due on 

March I for the previous calendar year. The certification need not include the period 

preceding the date the initial Title V permit was issued. Each compliance certification 

shall include: 

(A) Identification of each permit term or condition that is the basis of the certification; 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page: 8 

Facilitv ID: 800074 

Revision#: 8 

Date: January 14, 2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

(B) The compliance status during the reporting period; 

(C) Whether compliance was continuous or intermittent; 

(D) The method(s) used to determine compliance over the reporting period and 

currently, and 

(E) Any other facts specifically required by the Executive Officer to determine 

compliance. 

The EPA copy of the certification shall be sent to: Director of the Air Division Attn: 

Air-3 USEPA, Region IX 75 Hawthorne St. San Francisco, CA 94105 [3004(a)(I O)(E)] 

25. All records, reports, and documents required to be submitted by a Title V operator to 

AQMD or EPA shall contain a certification of accuracy consistent with Rule 3003(c)(7) 

by a responsible official (as defined in Rule 3000). [3004(a)(12)] 

PERIODIC MONITORING 

26. All periodic monitoring required by this permit pursuant to Rule 3004(a)(4)(c) is based 

on the requirements and justifications in the AQMD document "Periodic Monitoring 

Guidelines for Title V Facilities" or in case-by-case determinations documented in the 

TitleVapplication file. [3004(a)(4)] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

Section K Page: 9 

Facility ID: 800074 

Revision #: 8 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

FACILITY RULES 

This facility is subject to the following rules and regulations 

With the exception of Rule 402, 473, 477, 1118 and Rules 1401 through 1420, the following 

rules that are designated as non-federally enforceable are pending EPA approval as part of the 

state implementation plan. Upon the effective date of that approval, the approved rule(s) will 

become federally enforceable, and any earlier versions of those rules will no longer be federally 

enforceable. 

RULE SOURCE Adopted/Amended Date FEDERAL Enforceability 

RULE 1110.2 2-1-2008 Federally enforceable 

RULE 1113 11-8-1996 Federally enforceable 

RULE 1113 7-13-2007 Federally enforceable 

RULE 1140 2-1-1980 Federally enforceable 

RULE 1140 8-2-1985 Non federally enforceable 

RULE 1171 11-7-2003 Federally enforceable 

RULE 1171 2-1-2008 Federally enforceable 

RULE 118 12-7-1995 Non federally enforceable 

RULE 1303(a)(I )-BACT 12-6-2002 Non federally enforceable 

RULE 1303(a)(l)-BACT 5-10-1996 Federally enforceable 

RULE 1303(b)(l)-Modeling 12-6-2002 Non federally enforceable 

RULE 1303(b)(l)-Modeling 5-10-1996 Federally enforceable 

RULE 1303(b)(2)-0ffset 12-6-2002 Non federally enforceable 

RULE 1303(b)(2)-0ffset 5-10-1996 Federally enforceable 

RULE 1304(a)-Modeling and 6-14-1996 Federally enforceable 

Offset Exemption 

RULE 1304(c)-Offset 6-14-1996 Federally enforceable 

Exemption 

RULE 1411 3-1-1991 Non federally enforceable 

RULE 1470 5-4-2012 Non federally enforceable 

RULE 1470 6-1-2007 Non federally enforceable 

RULE 1703 - PSD Analysis 10-7-1988 Federally enforceable 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

Section K 

Facilitv ID: 

Revision#: 

Page: 10 

800074 

8 

Date: January 14, 2015 

FACILITY PERMIT TO OPERATE 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

RULE SOURCE Adopted/Amended Date FEDERAL Enforceability 

RULE2005 4-20-2001 Federally enforceable 

RULE2005 4-9-1999 Federally enforceable 

RULE2005 6-3-2011 Federally enforceable 

RULE2009 5-11-2001 Non federally enforceable 

RULE2012 12-5-2003 Federally enforceable 

RULE2012 5-11-2001 Federally enforceable 

RULE 2012 5-6-2005 Federally enforceable 

RULE204 10-8-1993 Federally enforceable 

RULE 217 1-5-1990 Federally enforceable 

RULE 218 5-14-1999 Federally enforceable 

RULE 218 8-7-198 l Federally enforceable 

RULE 219 9-4-1981 Federally enforceable 

RULE 3002 11-14-1997 Federally enforceable 

RULE 3003 11-14-1997 Federally enforceable 

RULE 3004(a)(4)-Periodic 12-12-1997 Federally enforceable 

Monitoring 

RULE3005 11-14-1997 Federally enforceable 

RULE 3007 10-8-1993 Federally enforceable 

RULE304 l-14-1982 Non federally enforceable 

RULE 401 11-9-2001 Non federally enforceable 

RULE 401 3-2-1984 Federally enforceable 

RULE402 5-7-1976 Non federally enforceable 

RULE404 2-7-1986 Federally enforceable 

RULE405 2-7-1986 Federally enforceable 

RULE407 4-2-1982 Federally enforceable 

RULE408 5-7-1976 Federally enforceable 

RULE409 8-7-1981 Federally enforceable 

RULE430 7-12-1996 Non federally enforceable 

RULE 431.l 11-17-1995 Non federally enforceable 

RULE 431.2 5-4-1990 Federally enforceable 

RULE 431.2 9-15-2000 Non federally enforceable 

RULE463 3-11-1994 Federally enforceable 

RULE464 12-7-1990 Federally enforceable 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Section K Page: 11 

Facilitv lD: 800074 

Revision#: 8 

Date: January 14,2015 

LA CITY, DWP HAYNES GENERATING STATION 

SECTION K: TITLE V Administration 

RULE SOURCE Adopted/Amended Date FEDERAL Enforceability 

RULE475 10-8-1976 Federally enforceable 

RULE 475 8-7-1978 Non federally enforceable 

RULE 701 6-13-1997 Federally enforceable 

CAPRCCEQA 11-23-1970 Non federally enforceable 

40CFR 60 Subpart Da 10-4-1991 Federally enforceable 

40CFR 60 Subpart GG 3-6-1981 Federally enforceable 

40CFR 60 Subpart III! 7-11-2006 Federally enforceable 

40CFR 60 Subpart KKKK 7-6-2006 Federally enforceable 

40CFR 63 Subpart ZZZZ 1-30-2013 Federally enforceable 

40CFR 68 - Accidental 5-24-1996 Federally enforceable 

Release Prevention 

40CFR 72 - Acid Rain 11-24-1997 Federally enforceable 

Provisions 

40CFR 73 Subpart B 1-11-1993 Federally enforceable 

40CFR 82 Subpart B 7-14-1992 Federally enforceable 

40CFR Part 51, Appendix S 10-20-2010 Federally enforceable 
South Coast Air Quality Management District 

2 t 865 Copley Drive, Diamond Bar, CA 91 765-4 t 78 

FACILITY PERMIT TO OPERATE 

Appendix A Page: I 

Facilitv JD· 800074 

Revision#: 9 

Date: January 14. 2015 

LA CITY, DWP BAYNES GENERATING STATION 

APPENDIX A: NOX AND SOX EMITTING EQUIPMENT EXEMPT FROM WRITTEN 

PERMIT PURSUANT TO RULE 219 

1. VACUUM, GASOLINE 

2. BACKPACK AIR BLOWER, GASOLINE 

3. CHAIN SAW, GASOLINE 

4. CONCRETE SAW, GASOLINE 

5. AIR COMPRESSOR, GASOLINE 

6. CONCRETE MIXERS, GASOLINE 

7. WELDER, GASOLINE 

8. WATER BLASTER, GASOLINE 

9. IC ENGINES 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91 765-41 78 

Appendix B Page: I 

Facilitv ID: 800074 

Revision#: 1 

Date: January 14. 2015 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1113 11-08-1996) 

(I) Except as provided in paragraphs (c)(2), (c)(3), and (c)(4) of Rule 

1113, the operator shall not supply, sell, offer for sale, apply, or solicit 

the application of, any architectural coating which, at the time of sale or 

manufacture, contains more than 250 grams ofVOe per liter of coating 

(2.08 pounds per gallon), less water, Jess exempt compounds, and less 

any colorant added to tint bases, or manufacture, blend, or repackage 

such a coating for use within the District. 

(2) Except as provided in paragraphs (c)(3) and (c)(4) of Rule 1113, the 

operator shall not supply, sell, offer for sale, apply, solicit the 

application of, manufacture, blend, or repackage, for use within the 

District, any architectural coating listed in the Table of Standards which 

contains voe (excluding any colorant added to tint bases) in excess of 

the corresponding voe limit specified in the table, after the effective 

date specified. 

TABLE OF STANDARDS 

VOCLIMITS 

Grams ofVOC Per Liter of Coating, 

Less Water And Less Exempt Compounds 

COATING Limit* Effective Effective Effective Effective Effective Effective 

Date of 1/1/1998 111/1999 7/1/2001 1/1/2005 7/112008 

Adootion 

Bond Breai<ers 350 

Clear Wood Finishes 

Varnish 350 

Sanding Sealers 350 

Lacquer 680 550 275 

Concrete-Curing Compounds 350 

Dry-Fog Coatings 400 

Fire-proofing Exterior 350 450 350 

Coatmgs 

Fire-Retardant Coatings 

Clear 650 

Pigmented 350 

Flats 250 100 so 

Graphic Arts (Sign) Coatings 500 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

Industrial Maintenance 

Primers and Topcoats 

Alkyds 

Catalyzed Epoxy 

Bituminous Coatings 

Materials 

Inorganic Po~ers 

Vinyl Chlori e Polymers 

Chlorinated Rubber 

Acrylic Polymers 

Urethane Polymers 

Silicones 

Unique Vehicles 

Japans/Faux Finishing 

Coatings 

Magnesite Cement Coatings 

Mastic Coatings 

Metallic Pigmented Coatings 

Multi-Color Coatings 

APPENDIX B: RULE EMISSION LIMITS 

!RULE 1113 11-08-1996) 

420 

420 

420 

420 

420 

420 

420 

420 

420 

420 

350 700 350 

600 450 

300 

500 

420 250 

Appendix B Page: 2 

Facility ID 800074 

Revision#: 7 

Date: January 14.2015 

Pigmented Lacquer 680 550 275 

Pre-Treatment Wash Primers 780 

Primers, Sealers, and 350 

Undercoaters 

Quick-Dry Enamels 400 

Roof Coatings 300 

Shellac 

Clear 730 

Pigmented 550 

Stains 350 

Swimming Pool Coatings 

Repair 650 

Other 340 

Traffic Coatings 250 150 

Waterproofmg Sealers 400 

Wood Preservatives 

Below-Ground 350 

Other 350 

* The specified hmits remam in effect unless revised limits are listed in subsequent columns m the Table of Standards 

TABLE OF STANDARDS (cont.) 

VOCLIMITS 

Grams of VOC Per Liter of Material 

COATING 

Low-Solids Coating 

Limit 

120 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HA YNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1113 07-13-20071 

(1) Except as provided in paragraphs (c)(2), (c)(3), (c)(4), and specified coatings 

averaged under ( c )( 6), no person shall supply, sell, offer for sale, 

manufacture, blend, or repackage any architectural coating for use in the 

District which, at the time of sale or manufacture, contains more than 250 

grams of voe per liter of coating (2.08 pounds per gallon), less water, less 

exempt compounds, and less any colorant added to tint bases, and no person 

shall apply or solicit the application of any architectural coating within the 

District that exceeds 250 grams of VOC per liter of coating as calculated in 

this paragraph. 

(2) Except as provided in paragraphs (c)(3), (c)(4), and designated coatings 

averaged under ( c )( 6), no person shall supply, sell, offer for sale, 

manufacture, blend, or repackage, for use within the District, any 

architectural coating listed in the Table of Standards which contains VOC 

(excluding any colorant added to tint bases) in excess of the corresponding 

voe limit specified in the table, after the effective date specified, and no 

person shall apply or solicit the application of any architectural coating 

within the District that exceeds the VOC limit as specified in this paragraph. 

No person shall apply or solicit the application within the District of any 

industrial maintenance coatings, except anti-graffiti coatings, for residential 

use or for use in areas such as office space and meeting rooms of industrial, 

commercial or institutional facilities not exposed to such extreme 

environmental conditions described in the definition of industrial 

maintenance coatings; or of any rust-preventative coating for industrial use, 

unless such a rust preventative coating complies with the Industrial 

Maintenance Coating VOC limit specified in the Table of Standards. 

Appendix B Page: 3 

Facility ID: 800074 

Revision#: 7 

Date: January 14, 2015 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1113 07-13-2007] 

TABLE OF STANDARDS 

VOCLIMITS 

Grams ofVOC Per Liter of Coating, 

Less Water and Less Exempt Compounds 

'' COA'ltNG CA:;TEGOltY .. ~g '1Zui'rent ye.. . ~;;c >~!Tecllv~l)(lte - :" ;_ - -, J)ilnjt• >Lbnit .·· 

i!:I>~. ~iJJD,t ---k'·'iX<'. ~ - :!IJP~ 7~\l!Ji 

Bond Breakers 350 

Clear Wood Finishes 350 275 

Varnish 350 275 

Sanding Sealers 350 275 

Lacquer 680 550 275 

Clear Brushing Lacquer 680 275 

Concrete-Curing Compounds 3SO 

Concrete-Curing Compounds 3SO 

For Roadways and 

Bridges** 

Drv-Fog Coatings 400 

Fire-Proofing Exterior Coatings 4SO 350 

Fire-Retardant Coatings*** 

Clear 6SO 

Pigmented 3SO 

Flats 2SO 100 

Floor Coatings 420 100 50 

Graphic Arts !Si on\ Coatinos SOD 

Industrial Maintenance (IM) 420 2SO 100 

Coatings 

High Temperature IM 420 

Coatings 

Zinc-Rich IM Primers 420 340 100 

Japans/Faux Finishing Coatings 700 350 

Magnesite Cement Coatings 600 450 

Mastic Coatings 300 

Metallic Pigmented Coatings SOD 

Multi-Color Coatings 420 2SO 

Nonflat Coatings 250 ISO 50 

Appendix B Page: 4 

Facilitv ID· 800074 

Revision #: 7 

Date: January 14,2015 

~Fr' 'T 

7/~, "c • k: i~ 

100 

ISO 

so 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1113 07-13-2007) 

Nonflat High Gloss 

Pigmented Lacquer 

Pre-Treatment Wash Primers 

Primers, Sealers, and 

Undercoaters 

Quick-Dry Enamels 

Quick-Dry Primers, Sealers, 

and U ndercoaters 

Recycled Coatings 

Roof Coatings 

Roof Coatings, Aluminum 

Roof Primers, Bituminous 

Rust Preventative Coatin s 

Shellac 

Clear 

Stains, Interior 

Swimming Pool Coatings 

Repair 

Other 

Traffic Coatings 

Waterproofing 

Concrete/Masonry Sealers 

Wood Preservatives 

Below-Ground 

Other 

250 

680 

780 

350 

400 

350 

300 

500 

350 

420 

730 

550 

350 

350 

250 

650 

340 

250 

400 

400 

350 

350 

550 

150 

150 

420 

200 

250 

200 

250 

250 

350 

400 

250 

340 

250 

275 

50 

100 

100 

150 

100 

100 

250 

100 

100 

Appendix B Page: 5 

Facility ID: 800074 

Revision#: 7 

Date: January 14, 2015 

50 

50 

100 

100 

100 

• The specified limits remain in effect unless revised limits are listed in subsequent columns in the Table of 

Standards. 

** Does not include compounds used for curbs and gutters, sidewalks, islands, driveways and other 

miscellaneous concrete areas. 

*** The Fire-Retardant Coating category will be eliminated on January 1, 2007 and subsumed by the 

coating category for which they are formulated. 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1113 07-13-2007) 

TABLE OF STANDARDS (cont.) 

VOCLIMITS 

Grams of VOC Per Liter of Material 

I COATING 

Low-Solids Coating 

Limit 

120 

Appendix B Page: 6 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14, 2015 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1140 02-01-1980] 

(1) The operator shall not, if he complies with an applicable performance 

standard in section (b)(4) of Rule 1140, discharge into the atmosphere from 

any abrasive blasting any air contaminant for a period or periods aggregating 

more than three minutes in any one hour which is: 

(A) As dark or darker in shade as that designated as No. 2 on the 

Ringelmann Chart, as published by the United States Bureau of 

Mines, or 

(B) Of such opacity as to obscure an observer's view to a degree equal to 

or greater than does smoke described in (1 )(A). 

(2) The operator shall not, ifhe is not complying with an applicable performance 

standard in section (b)(4) of Rule 1140, discharge into the atmosphere from 

any abrasive blasting any air contaminant for a period or periods aggregating 

more than three minutes in any one hour which is: 

(A) As dark or darker in shade as that designated as No. 1 on the 

Ringelmann Chart, as published by the United States Bureau of 

Mines, or 

(B) Of such opacity as to obscure an observer's view to a degree equal to 

or greater than does smoke described in (2)(A). 

Appendix B Page: 7 

Facilitv ID: &00074 

Revision#: 7 

Date: January 14, 2015 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1140 08-02-1985] 

(I) The operator shall not, if he complies with an applicable performance 

standard in section (b)(4) of Rule 1140, discharge into the atmosphere from 

any abrasive blasting any air contaminant for a period or periods aggregating 

more than three minutes in any one hour which is: 

(A) As dark or darker in shade as that designated as No. 2 on the 

Ringelmann Chart, as published by the United States Bureau of 

Mines, or 

(B) Of such opacity as to obscure an observer's view to a degree equal to 

or greater than does smoke described in (l)(A). 

(2) The operator shall not, ifhe is not complying with an applicable performance 

standard in section (b)(4) of Rule 1140, discharge into the atmosphere from 

any abrasive blasting any air contaminant for a period or periods aggregating 

more than three minutes in any one hour which is: 

(A) As dark or darker in shade as that designated as No. 1 on the 

Ringelmann Chart, as published by the United States Bureau of 

Mines, or 

(B) Of such opacity as to obscure an observer's view to a degree equal to 

or greater than does smoke described in (2)(A). 

Appendix B Page: 8 

Facility ID: 800074 

Revision#: 7 

Date: January 14, 2015 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix 8 Page: 9 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14, 2015 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 117111-07-2003) 

(1) Solvent Requirements 

A person shall not use a solvent to perform solvent cleaning operations unless the 

solvent complies with the applicable requirements set forth below: 

CURRENT 

LIMITS 

SOL VENT CLEANING ACTIVITY voe 

g/l 

(lb/gal) 

(A) Product Cleaning During Manufacturing Process Or Surface 

Preparation For Coating, Adhesive, Or Ink Application 

(i) General 25 

(0.21) 

(ii) Electrical Apparatus Components & Electronic 500 

Components (4.2) 

(iii) Medical Devices & Pharmaceuticals 800 

(6.7) 

(B) Repair and Maintenance Cleaning 

(i) General 25 

(0.21) 

(ii) Electrical Apparatus Components & 900 

Electronic Components (7.5) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 10 

Facility ID: 800074 

Revision#· 7 

Date: January 14, 2015 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 117111-07-2003) 

SOLVENT CLEANING ACTNITY 

(iii) Medical Devices & Pharmaceuticals 

(A) Tools, Equipment, & Machinery 

(B) General Work Surfaces 

(C) Cleaning of Coatings or Adhesives Application 

Equipment 

(D) Cleaning of Ink Application Equipment 

(i) General 

(ii) Flexographic Printing 

(iii) Gravure Printing 

(A) Publication 

(B) Packaging 

(iv) Lithographic or Letter Press Printing 

CURRENT 

LIMITS 

voe 

g/l 

(lb/gal) 

800 

(6.7) 

600 

(5.0) 

550 

(4.6) 

25 

(0.21) 

25 

(0.21) 

750 

(6.3) 

25 

(0.21) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 11 

Facility ID: 800074 

Revision#: 7 

Date: January 14,2015 

LA CITY. DWP HAYNES GENERATING STATION 

(v) 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 117111-07-2003) 

SOL VENT CLEANING ACTMTY 

(A) Roller Wash - Step 1 

(B) Roller Wash-Step 2, 

Blanket Wash, & On-Press Components 

(C) Removable Press Components 

Screen Printing 

(vi) Ultraviolet fuk/ Electron Beam fuk 

Application Equipment (except screen printing) 

(vii) Specialty Flexographic Printing 

(E) Cleaning of Polyester Resin Application Equipment 

CURRENT 

LIMITS 

voe 

g/l 

(lb/gal) 

600 

(5.0) 

800 

(6.7) 

25 

(0.21) 

750 

(6.3) 

800 

(6.7) 

600 

(5.0) 

25 

(0.21) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 12 

Facility ID: 800074 

Revision#: 7 

Date: January 14, 2015 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1171 02-01-2008] 

(1) Solvent Requirements 

A person shall not use a solvent to perform solvent cleaning operations unless the 

solvent complies with the applicable requirements set forth below: 

. 

CURRENT EFFECTlVE EFFECTIVE 

LIMITS* 11112008* 11112009 

voe voe voe 

SOLVENT CLEANING ACTIVITY g/I g/I g/I 

. (lb/eal) (lb/eal). . (lb/eal) 

(A) Product Cleaning During 

Manufacturing Process Or Surface 

Preparation For Coating, Adhesive, 

Or Ink Application 

(i) General 25 

(0.21) 

(ii) Electrical Apparatus 100 

Components & Electronic (0.83) 

Components 

(iii) Medical Devices & 800 

Pharmaceuticals (6.7) 

(B) Repair and Maintenance Cleaning 

(i) General 25 

(0.21) 

(ii) Electrical Apparatus 100 

Components & Electronic (0.83) 

Components 
South Coast Air Quality Management District 

21865 Copley Drive. Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 13 

Facilitv ID: 800074 

Revision # · 7 

Date: January 14, 2015 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1171 02-01-2008) 

CURRENT EFFECTIVE 

LIMITS* 1/112008* 

voe voe 

SOLVENT CLEANING ACTIVITY g/I g/I 

(cont.) (lb/gal) (lb/gal) 

(iii) Medical Devices & 

Pharmaceuticals 

(A) Tools, Equipment, & 800 

Machinery (6.7) 

(B) General Work Surfaces 600 

(5.0) 

(C) Cleaning of Coatings or Adhesives 25 

Application Equipment (0.21) 

(D) Cleaning of Ink Application 

Equipment 

(i) General 25 

(0.21) 

(ii) Flexographic Printing 25 

(0.21) 

(iii) Gravure Printing 

(A) Publication 100 

(0.83) 

(B) Packaging 25 

(0.21) 

(iv) Lithographic (Offset) or Letter Press 

Printing 

(A) Roller Wash, Blanket Wash, 

& On-Press Components 

(I) Newsprint 100 

(0.83) 

EFFECTIVE 

1/112009 

voe 

g/I 

(lb/gal) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-41 78 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 14 

Facility ID: 800074 

Revision#: 7 

Date: January 14,2015 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 1171 02-01-20081 

CURRENT EFFECTIVE 

LIMITS* 1/112008* 

voe voe 

SOLVENT CLEANING ACTIVITY g/I g/I 

(cont.) (lb/gal) (lb/gal) 

(II) Other Substrates 500 100 

(4.2) (0.83) 

(B) Removable Press Components 25 

(021) 

(v) Screen Printing 500 100 

(42) (0.83) 

(vi) Ultraviolet fuk/ Electron Beam Ink 650 650 

Application Equipment (except (5.4) (5.4) 

screen printing) 

(vii) Specialty Flexographic Printing 100 

(083) 

(E) Cleaning of Polyester Resin Application 25 

Equipment (0.21) 

EFFECTIVE 

1/112009 

voe 

g/I 

(lb/gal) 

100 

(0.83) 

* The specified hm1ts remam m effect unless revised hm1ts are hsted m subsequent 

columns. 
South Coast Air Quality Management District 

Z 1865 Copley Drive. Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 15 

Facility ID: 800074 

Revision#: 7 

Date: January 14. 2015 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 404 02-07-1986) 

The operator shall not discharge into the atmosphere from this equipment, particulate 

matter in excess of the concentration at standard conditions, shown in Table 404(a). 

Where the volume discharged is between figures listed in the Table, the exact 

concentration permitted to be discharged shall be determined by linear interpolation. 

For the purposes of this rule, emissions shall be averaged over one complete cycle of 

operation or one hour, whichever is the lesser time period. 

TABLE 404(a) 

Maximum Concentration Maximum Concentration 

of Particulate of Particulate Matter 

Volume Discharged Matter" Allowed in Volume Discharged Allowed in Discharged 

Calculated as Dry Discharged Gas Calculated as Dry Gas Gas Calculated as Dry Gas 

Gas Calculated as Dry At Standard Conditions at 

At Standard Gas at Standard Standard Conditions 

Conditions Conditions 

Cubic Cubic Milligrams Grains per Cubic Cubic Milligrams Grains per 

meters feet per Cubic Foot meters feet per Cubic 

Per Per Cubic Per Minute Per Cubic Meter Foot 

Minute Minute Meter Minute 

25 or 883 450 0.196 900 31780 118 0.0515 

or 

less less 

30 1059 420 .183 1000 35310 113 .0493 

35 1236 397 .173 1100 38850 109 .0476 

40 1413 377 .165 1200 42380 106 .0463 

45 1589 361 .158 1300 45910 102 .0445 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 16 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14, 2015 

LA CITY. DWP HAYNES GENERATING STATION 

Volume Discharged 

Calculated as Dry 

Gas 

At Standard 

Conditions 

Cubic Cubic 

meters feet 

Per Per 

Minute Minute 

50 1766 

60 2119 

70 2472 

80 2825 

90 3178 

100 3531 

125 4414 

150 5297 

175 6180 

200 7063 

250 8829 

300 10590 

350 12360 

400 14130 

450 15890 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 404 02-07-1986] 

Maximum Concentration 

of Particulate 

Matter" Allowed in Volume Discharged 

Discharged Gas Calculated as Dry Gas 

Calculated as Dry At Standard Conditions 

Gas at Standard 

Conditions 

Milligrams Grains per Cubic Cubic 

per Cubic Foot meters feet 

Cubic Per Minute Per 

Meter Minute 

347 .152 1400 49440 

324 .141 1500 52970 

306 .134 1750 61800 

291 .127 2000 70630 

279 .122 2250 79460 

267 .117 2500 88290 

246 .107 3000 105900 

230 .100 4000 141300 

217 .0947 5000 176600 

206 .0900 6000 211900 

190 .0830 8000 282500 

177 .0773 10000 353100 

167 .0730 15000 529700 

159 .0694 20000 706300 

152 .0664 25000 882900 

Maximum Concentration 

of Particulate Matter 

Allowed in Discharged 

Gas Calculated as Dry Gas 

at 

Standard Conditions 

Milligrams Grains per 

per Cubic 

Cubic Meter Foot 

100 .0437 

97 .0424 

92 .0402 

87 .0380 

83 .0362 

80 .0349 

75 .0327 

67 .0293 

62 .0271 

58 .0253 

52 .0227 

48 .0210 

41 .0179 

37 .0162 

34 .0148 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix B Page: 17 

Facility ID· 800074 

Revision#: 7 

Date: January 14, 2015 

LA CITY. DWP HAYNES GENERATING STATION 

Volume Discharged 

Calculated as Dry 

Gas 

At Standard 

Conditions 

Cubic Cubic 

meters feet 

Per Per 

Minute Minute 

500 17660 

600 21190 

700 24720 

800 28250 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 404 02-07-1986) 

Maximum Concentration 

of Particulate 

Matter" Allowed in Volume Discharged 

Discharged Gas Calculated as Dry Gas 

Calculated as Dry At Standard Conditions 

Gas at Standard 

Conditions 

Milligrams Grains per Cubic Cubic 

per Cubic Foot meters feet 

Cubic Per Minute Per 

Meter Minute 

146 .0637 30000 1059000 

137 .0598 40000 1413000 

129 .0563 50000 1766000 

123 .0537 70000 2472000 

or more or more 

Maximum Concentration 

of Particulate Matter 

Allowed in Discharged 

Gas Calculated as Dry Gas 

at 

Standard Conditions 

Milligrams Grains per 

per Cubic 

Cubic Meter Foot 

32 .0140 

28 .0122 

26 .0114 

23 .0100 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix B Page· 18 

Facilitv ID: 800074 

Revision#· 7 

Date: January 14,2015 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 405 02-07-1986) 

The operator shall not discharge into the atmosphere from this equipment, solid 

particulate matter including lead and lead compounds in excess of the rate shown in 

Table 405(a). 

Where the process weight per hour is between figures listed in the table, the exact 

weight of permitted discharge shall be determined by linear interpolation. 

For the purposes of this rule, emissions shall be averaged over one complete cycle of 

operation or one hour, whichever is the lesser time period. 

TABLE 405(a) 

Maximum Discharge Maximum Discharge Rate 

Rate Allowed for Solid 

Allowed for Solid Particulate Matter 

Process Weight Particulate Matter Process Weight (Aggregate Discharged 

Per Hour (Aggregate Per Hour From All points of 

Discharged From All Process 

Points of 

Process 

Kilograms Pounds Kilograms Pounds Kilograms Pounds Kilograms Pounds 

Per Hour Per Hour Per Hour Per Hour Per Hour Per Hour Per Hour Per Hour 

100 or 220 or 0.450 0.99 9000 19840 5.308 11.7 

less 

less 

150 331 0.585 1.29 10000 22050 5.440 12.0 

200 441 0.703 1.55 12500 27560 5.732 12.6 

250 551 0.804 1.77 15000 33070 5.982 13.2 

300 661 0.897 1.98 17500 38580 6.202 13.7 

350 772 0.983 2.17 20000 44090 6.399 14.1 

400 882 1.063 2.34 25000 55120 6.743 14.9 

450 992 1.138 2.51 30000 66140 7.037 15.5 

500 1102 1.209 2.67 35000 77160 7.296 16.1 

600 1323 1.340 2.95 40000 88180 7.527 16.6 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

Appendix 8 Page: I 9 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14. 2015 

LA CITY. DWP HAYNES GENERATING STATION 

Process Weight 

Per Hour 

Kilograms Pounds 

Per Hour Per Hour 

700 1543 

800 1764 

900 1984 

1000 2205 

1250 2756 

1500 3307 

1750 3858 

2000 4409 

2250 4960 

2500 5512 

2750 6063 

3000 6614 

3250 7165 

3600 7716 

4000 8818 

4500 9921 

5000 11020 

6000 13230 

7000 15430 

8000 17640 

APPENDIX B: RULE EMISSION LIMITS 

[RULE 405 02-07-1986] 

Maximum Discharge 

Rate 

Allowed for Solid 

Particulate Matter Process Weight 

(Aggregate Per Hour 

Discharged From All 

Points of 

Process 

Kilograms Pounds Kilograms Pounds 

Per Hour Per Hour Per Hour Per Hour 

1.461 3.22 45000 99210 

1.573 3.47 50000 110200 

1.678 3.70 60000 132300 

1.777 3.92 70000 154300 

2.003 4.42 80000 176400 

2.206 4.86 90000 198400 

2.392 5.27 100000 220500 

2.563 5.65 125000 275600 

2.723 6.00 150000 330700 

2.874 6.34 175000 385800 

3.016 6.65 200000 440900 

3.151 6.95 225000 496000 

3.280 7.23 250000 551200 

3.404 7.50 275000 606300 

3.637 8.02 300000 661400 

3.855 8.50 325000 716500 

4.059 8.95 350000 771600 

4.434 9.78 400000 881800 

4.775 10.5 450000 992100 

5.089 11.2 500000 1102000 

or more or more 

Maximum Discharge Rate 

Allowed for Solid 

Particulate Matter 

(Aggregate Discharged 

From All points of 

Process 

Kilograms Pounds 

Per Hour Per Hour 

7.738 17.1 

7.931 17.5 

8.277 18.2 

8.582 18.9 

8.854 19.5 

9.102 20.1 

9.329 20.6 

9.830 21.7 

10.26 22.6 

10.64 23.5 

10.97 24.2 

11.28 24.9 

11.56 25.5 

11.82 26.1 

12.07 26.6 

12.30 27.1 

12.51 27.6 

12.91 28.5 

13.27 29.3 

13.60 30.0 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP BAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[40CFR 72 -Acid Rain Provisions 11-24-1997) 

Appendix B Page: 20 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14, 2015 

I. A Title V permit revision is not required for emission increases that are authorized 

by allowances acquired under the Acid Rain Program, provided that the increases do 

not trigger a Title V permit revision under any other applicable requirement. [70.6 

(a)(4)(ii)] 

Monitoring Requirements 

2. The owners and operators and, to the extent applicable, the designated representative 

of each affected source and each affected unit at the source shall comply with the 

monitoring requirements as provided in 40 CFR Parts 74, 75, and 76. [40 CFR 

72.50, 72.31, 72.9(b)(l)) 

3. The emissions measurements recorded and reported in accordance with 40 CFR Part 

75 shall be used to determine compliance by the unit with the acid rain emissions 

limitations and emissions reduction requirements for sulfur dioxide (S02) under the 

Acid Rain Program. [40 CFR 72.9(b)(2), 40 CFR 75.2) 

4. The requirements of 40 CFR Parts 74 and 75 shall not affect the responsibility of the 

operator to monitor emissions of other pollutants or other emissions characteristics at 

the unit under other applicable requirements and other provisions of this permit. 

[40 CFR 72.9(b)(3), 40 CFR 72.5) 

Sulfur Dioxide Requirements 

5. The owners and operators of each source and each affected unit at the source shall: 

(A) Hold allowances, as of the allowance transfer deadline, in the unit's compliance 

subaccount (after deductions under 40 CFR Part 73, Section 73.34(C)) not less than 

the total annual emissions of S02 for the previous calendar year from the unit; and, 

[40 CFR 72.9(c)(i)], 

(B) Comply with the applicable acid rain emissions limitations for SOi.(40 CFR 

72.9(c)(ii)) 

6. Each ton of S02 emitted in excess of the acid rain emissions limitations for sulfur 

dioxide shall constitute a separate violation of the Act. [40 CFR 72.9(g)(7)) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO O.PERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

(40CFR 72 -Acid Rain Provisions 11-24-1997) 

Appendix B Page: 21 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14, 2015 

7. S02 allowances shall be held in, deducted from, or transferred among allowance 

tracking system accounts in accordance with the Acid Rain Program. [ 40 CFR 

72.9(g)(4)) 

8. A S02 allowance shall not be deducted in order to comply with the requirements 

under paragraph 41 (A) of the S02 requirements prior to the calendar year for which 

the allowance was allocated. [40 CFR 72.9(g)(S)) 

9. An affected unit shall be subject to the S02 requirements under the Acid Rain 

Program as follows:[40 CFR 72.6(a)] 

(A) Starting January 1, 2000, an affected unit under 40 CFR Part 72, Section 

72.6(a)(2); or [40 CFR 72.6(a)(2)) 

(B) Starting on the later of January I, 2000 or the deadline for monitor certification 

under 40 CFR Part 75, an affected unit under 40 CFR Part 72, Section 72.6(a)(3). 

[40CFR 72 6(a)(3)) 

I 0. An allowance allocated by the EPA administrator under the Acid Rain Program is a 

limited authorization to emit S02 in accordance with the Acid Rain Program. No 

provision of the Acid Rain Program, the acid rain permit application, the acid rain 

permit, or the written exemption under 40 CFR Part 72, Sections 72.7, 72.8, or 

72.14, and no provision of law shall be construed to limit the authority of the United 

States to terminate or limit such authorization. [40 CFR 72.9 (c)(6)) 

11. An allowance allocated by the EPA Administrator under the Acid Rain Program 

does not constitute a property right. [40 CFR 72.9(c)(7)) 

Excess Emissions Reguirements 

12. The designated representative of an affected unit that has excess emissions in any 

calendar year shall submit a proposed offset plan, as required under 40 CFR Part 77. 

[40 CFR 72 9(e)) 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX 8: RULE EMISSION LIMITS 

(40CFR 72 -Acid Rain Provisions 11-24-1997) 

Appendix B Page: 22 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14.2015 

13. The owners and operators of an affected unit that has excess emissions in any 

calendar year shall: [40 CFR 72.9(e)(2)] 

(A) Pay without demand the penalty required, and pay upon demand the interest on 

that penalty, as required by 40 CFR Part 77; and[40 CFR 72.9(e)(2)(i)] 

(B) Comply with the terms of an approved offset plan, as required by 40 CFR Part 

77. [40 CFR 72.9(e)(2)(ii)] 

Recordkeeping and Reporting Reguirements 

14. Unless otherwise provided, the owners and operators of the source and each affected 

unit at the source that are subject to the acid rain provisions under Title IV shall keep 

on site at the source each of the following documents for a period of five years from 

the date the document is created. This period may be extended for cause, at any time 

prior to the end of five years, in writing by the EPA Administrator or the Executive 

Officer: [40 CFR 72.9(t)(I)] 

(A) The certificate of representation for the designated representative for the source 

and each affected unit at the source and all documents that demonstrate the truth of 

the statements in the certificate of representation, in accordance with 40 CFR 72.24; 

provided that the certificate and documents shall be retained on site at the source 

beyond such five year period until such documents are superseded because of the 

submission of a new certificate of representation changing the designated 

representative; [40 CFR 72.9(f)(l )(i)] 

(B) All emissions monitoring information, in accordance with 40 CFR Part 75; [40 

CFR 72.9(t)(i)(ii)] 

(C) Copies of all reports, compliance certifications, and other submissions and all 

records made or required under the Acid Rain Program; and, [40 CFR 72.9(f)(l )(iii)] 

(D) Copies of all documents used to complete an acid rain permit application and 

any other submission under the Acid Rain Program or to demonstrate compliance 

with the requirements of the Acid Rain Program. [40 CFR 72.9(t)(l)(iv)] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar. CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[40CFR 72 -Acid Raio Provisions 11-24-1997) 

Appendix B Page: 23 

Facilitv ID: 800074 

Revision#: 7 

Date: January 14,2015 

1 S. The designated representative of an affected source and each affected unit at the 

source shall submit the reports and compliance certifications required under the Acid 

Rain Program, including those under 40 CFR Part 72 Subpart I and 40 CFR Part 75. 

[40 CFR 72. 9(t)(2)] 

Liability 

16. Any person who knowingly violates any requirement or prohibition of the Acid Rain 

Program, a complete acid rain permit application, an acid rain permit, or a written 

exemption under 40 CFR Part 72, Sections 72.7, 72.8, or 72.14, including any 

requirement for the payment of any penalty owed to the United States, shall be 

subject to enforcement pursuant to Section l 13(c) of the Act. [40 CFR 72.9 (g)(l)] 

17. Any person who knowingly makes a false, material statement in any record, 

submission, or report under the Acid Rain Program shall be subject to criminal 

enforcement pursuant to Section l 13(c) of the Act and 18 U.S.C. 1001. [40 CFR 

72.9 (g)(2)] 

18. No permit revision shall excuse any violation of the requirements of the Acid Rain 

Program that occurs prior to the date that the revision takes effect. [40 CFR 72.9 

(g)(3)] 

19. Each affected source and each affected unit shall meet the requirements of the Acid 

Rain Program. [40 CFR 72.9 (g)(4)] 

20. Any provision of the Acid Rain Program that applies to an affected source (including 

a provision applicable to the designated representative of an affected source) shall 

also apply to the owners and operators of such source and of the affected units at the 

source. [40 CFR 72.9 (g)(S)] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP BAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[40CFR 72 -Acid Rain Provisions 11-24-19971 

Appendix B Page: 24 

Facility ID: 800074 

Revision#: 7 

Date: Jam.1ary 14, 2015 

21. Any provision of the Acid Rain Program that applies to an affected unit (including a 

provision applicable to the designated representative of an affected unit) shall also 

apply to the owners and operators of such unit. Except as provided under 40 CFR 

Part 72, Section 72.44 (Phase II repowering extension plans) and 40 CFR Part 76, 

Section 76.11 (NOx averaging plans), and except with regard to the requirements 

applicable to units with a common stack under 40 CFR Part 75 (including 40 CFR 

Part 75, Sections 75.16, 75.17, and 75.18), the owners and operators and the 

designated representative of one affected unit shall not be liable for any violation by 

any other affected unit of which they are not owners or operators or the designated 

representative and that is located at a source of which they are not owners or 

operators or the designated representative. [40 CFR 72.9 (g)(6)] 

22. Each violation of a provision of 40 CFR Parts 72, 73, 74, 75, 76, 77, and 78 by an 

affected source or affected unit, or by an owner or operator or designated 

representative of such source or unit, shall be a separate violation of the Act. [ 40 

CFR 72.9 (g)(7)] 

Effect on Other Authorities 

23. No provision of the Acid Rain Program, an acid rain permit application, an acid rain 

permit, or a written exemption under 40 CFR Part 72, Sections 72.7, 72.8, or 72.14 

shall be construed as: [40 CFR 72.9 (h)] 

(A) Except as expressly provided in Title IV of the Act, exempting or excluding the 

owners and operators and, to the extent applicable, the designated representative of 

an affected source or affected unit from compliance with any other provision of the 

Act, including the provisions of Title I of the Act relating to applicable National 

Ambient Air Quality Standards or state implementation plans; [40 CFR 72. 9 (h)(l )] 

(B) Limiting the number of allowances a unit can hold; provided, that the number of 

allowances held by the unit shall not affect the source's obligation to comply with 

any other provisions of the Act; [40 CFR 72.9 (h)(2)] 
South Coast Air Quality Management District 

21865 Copley Drive, Diamond Bar, CA 91765-4178 

FACILITY PERMIT TO OPERATE 

LA CITY. DWP HAYNES GENERATING STATION 

APPENDIX B: RULE EMISSION LIMITS 

[40CFR 72 -Acid Rain Provisions 11-24-1997) 

(C) Requiring a change of any kind in any state law regulating electric utility rates 

and charges, affecting any state law regarding such state regulation, or limiting such 

state regulation, including any prudence review requirements under such state law; 

[40 CFR 72.9 (h)(3)] 

(D) Modifying the Federal Power Act or affecting the authority of the Federal 

Energy Regulatory Commission under the Federal Power Act; or, [40 CFR 72.9 

(h)(4)] 

(E) Interfering with or impairing any program for competitive bidding for power 

supply in a state in which such program is established. [40 CFR 72.9 (h)(5)] 

Appendix B Page: 25 

Facilitv ID: 800074 

Revision #: 7 

Date: January 14,2015