Title Page Facilitv ID· Revision#: 800074 54 

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Date· January 14,2015 

## FACILITY PERMIT TO OPERATE

LA CITY, DWP HAYNES GENERATING STATION 6801 2ND ST LONG BEACH, CA90803

NOTICE

IN ACCORDANCE WITH RULE 206, THIS PERMIT TO OPERATE OR A COPY THEREOF MUST BE KEPT AT THE LOCATlON FOR WHICH IT IS ISSUED. THIS PERMIT DOES NOT AUTHORIZE THE EMISSION OF AIR CONTAMINANTS IN EXCESS OF THOSE ALLOWED BY DIVISION 26 OF THE HEALTH AND SAFETY CODE OF THE STATE OF CALIFORNIA OR THE RULES OF THE SOUTH COAST AIR QUALITY MANAGEMENT DISTRICT. THIS PERMIT SHALL NOT BE CONSTRUED AS PERMISSION TO VIOLATE EXISTING LAWS, ORDINANCES, REGULATIONS OR STATUTES OF ANY OTHER FEDERAL, STATE OR LOCAL GOVERNMENTAL AGENCIES.

Barry R. Wallerstein, D. Env.

# ""Tome~

# By~&rf- Mohsen Nazemi, P.E. Deputy Executive Officer Engineering & Compliance

### Section A B 

# c D
E F
G
H


### I 1 

### K Appendix A



### B 

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Table ofContent Facilitv ID: 800074 Revision#: 54 Date: January 14, 2015



## LA CITY, DWP

## HAYNES GENERATING STATION

TABLE OF CONTENTS

Description Facility Information RECLAIM Annual Emission Allocation Facility PlotPlan Facility Description and Equipment Specific Conditions Administrative Conditions RECLAIM Monitoring and Source Testing Requirements Recordkeeping and Reporting Requirements for RECLAIM Sources PermitTo Construct and Temporary Permitto Operate Compliance Plans & 

### Schedules Air Toxics Title V Administration

NOx and SOx Emitting EquipmentExempt From Written Permit Pursuant to Rule 219 Rule Emission Limits Revision# Date Issued 15 01/14/2015 25 01/14/2015 TO BE DEVELOPED 28 01/14/2015
16 01/14/2015 12 01/14/2015
13 01/14/2015
30 01/14/2015


### JO 01/14/2015 

### 7 01/14/2015 8 01/14/2015



### 9 01/14/2015



### 7 01/14/2015

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-41 78 Section A Page: I Facilitv ID· 800074 Revision#: 15 Date: January 14,2015 

## FACILITYPERMITTO OPERATE LACITY,DWPHAYNES GENERATING STATION SECTIONA: FACILITYINFORMATION
LEGAL OWNER&/OROPERA TOR: LEGAL OPERATOR (ifdifferent than owner): EQUIPMENT LOCATION:

MAILING ADDRESS:

RESPONSIBLE OFFICIAL:
TITLE: TELEPHONENUMBER: CONTACT PERSON: TITLE:
TELEPHONE NUMBER: TITLE V 

### PERMIT ISSUED: TITLE V 

### PERMIT EXPIRATION DATE:

TITLE V

YES LA CITY, DWP HAYNES GENERA TING STATION

680I 2ND ST LONG BEACH, CA 90803-4324

P.O. BOX 51I11 RM# I050 LOS ANGELES, CA 9005I-5700 RANDY S. HOWARD

SENIORASSISTANT GENERAL MANAGER (2I3) 367-038I MARKJ. SEDLACEK
DIRECTOR OF ENVIRONMENTAL SERVICES (213) 367-0403 January I4, 2015 January I3, 2020



### RECLAIM

NOx: SOx: CYCLE: ZONE: YES NO l COASTAL

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4I78



## FACILITYPERMITTOOPERATE Section B Page: I Facilitv ID: 800074 Revision #· 25 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION SECTION B: RECLAIMANNUAL EMISSIONALLOCATION The annual allocation of NOx RECLAIM Trading Credits (RTCs) for this facility is calculated pursuant to Rule 2002. Total NOx emission shall not exceed such annual allocations unless the operator obtains RTCs corresponding to the facility's increased emissions in compliance with Rules 2005 and 2007. The level of Starting Allocation plus Non-Tradable Credits used to determine compliance with Rule 2005(c)(4) and applicability of Rule 2005(e)

- Trading Zone Restrictions is listed on the last page ofthis Section. The following table lists the annual allocations that were issued to this facility and the amounts of RTCs held by this facility on the day ofprinting this Section. 

### RECLAIM POLLUTANT ANNUAL ALLOCATION (POUNDS)
NOxRTC NOxRTC l Non-Tradable 2 Year Initially Holding as of Non-Usable Begin End Zone (month/year) Allocated 01114/2015 RTCs (pounds) (pounds) 112013 12/2013 Coastal 489016 186880 0 112014 12/2014 Coastal 489016 378987 0 112015 12/2015 Coastal 489016 378987 0 112016 12/2016 Coastal 489016 378987 0 112017 12/2017 Coastal 489016 378987 0 112018 12/2018 Coastal 489016 378987 0 112019 12/2019 Coastal 489016 378987 0 112020 12/2020 Coastal 489016 378987 0 1/2021 12/2021 Coastal 489016 378987 0 112022 12/2022 Coastal 489016 378987 0 112023 12/2023 Coastal 489016 378987 0 112024 12/2024 Coastal 489016 378987 0 !/2025 12/2025 Coastal 489016 378987 0 1/2026 12/2026 Coastal 489016 378987 0 !/2027 12/2027 Coastal 489016 378987 0 1/2028 12/2028 Coastal 489016 378987 0 !/2029 12/2029 Coastal 489016 378987 0 Footnotes: I. This number may change due to pending trades. emissions reported under Quarterly Certification of Emissions Report (QCER) and Annual Pennit Emission Program (APEP) Report required pursuant to Rule 2004. or deductions made pursuant to Rule 2010(b). The most recent total RTC information can be obtained from the District's RTC Listing. 2. The use ofsuch credits is subject to restrictions set forth in paragraph (t)(l) ofRule 2002.

## I~ South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-41 78


## FACILITYPERMITTO OPERATE Section B Page· 2 Facilitv ID: 800074 Revision #: 25 Date: January 14,2015



## LA CITY,DWPHAYNES GENERATING STATION SECTIONB: RECLAIM ANNUAL EMISSION ALLOCATION The annual allocation of NOx RECLAIM Trading Credits (RTCs) for this facility is calculated pursuant to Rule 2002. Total NOx emission shall not exceed such annual allocations unless the operator obtains RTCs corresponding to the facility's increased emissions in compliance with Rules 2005 and 2007. The level of Starting Allocation plus Non-Tradable Credits used to determine compliance with Rule 2005(c)(4) and applicability of Rule 2005(e)

- Trading Zone Restrictions is listed on the last page ofthis Section. The following table lists the annual allocations that were issued to this facility and the amounts of RTCs held by this facility on the day ofprinting this Section. 

### RECLAIM POLLUTANTANNUAL ALLOCATION (POUNDS)
NOxRTC NOxRTC I Non-Tradable Year Initially Holding as of Non-Usable Begin End Zone (month/year) Allocated 01/14/2015 RTCs (pounds) (pounds)
1/2030 12/2030 Coastal 489016 378987 0

Footnotes: I. This number may change due to pending trades, em1ss1ons reported under Quarterly Certification of Emissions Report (QCER) and Annual Permit Emission Program (APEP) Report required pursuant to Rule 2004, or deductions made pursuant to Rule 2010(b). The most recent total RTC information can be obtained from the District's RTC Listing. 2. The use ofsuch credits is subject to restrictions set forth in paragraph (t)(1) ofRule 2002. 

### 2

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178



## FACILITYPERMIT TOOPERATE Section B Page· 3 Facility JD 800074 Revision#: 25 Date: January 14, 2015



## LA CITY, DWPHAYNES GENERATING STATION

SECTION B: 

## RECLAIM ANNUAL EMISSIONALLOCATION The annual allocation of RECLAIM Trading Credits (RTCs) for this facility 1s calculated pursuant to Rule 2002. If the facility submits a permit application to increase in an annual allocation to a level greater than the facility's starting Allocation plus Non-Tradable credits as listed below, the application will be evaluated for compliance with Rule 2005 (c)(4). Rule 2005 (e)

- Trading Zone Restrictions applies if an annual allocation is increased to a level greater than the facility's Starting Allocation plus Non-Tradable Credits:

Year NOx RTC Non-Tradable Begin End Zone Starting Allocation Credits(NTC) (month/year) (pounds) (pounds) 

### 1/1994 12/1994 Coastal 

### 3666443 

### 0

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-41 78


## FACILITYPERMITTO OPERATE Section C Page: I Facility ID: 800074 Revision#: 8 Date· January 14,2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION C: FACILITYPLOT PLAN

(TO BE DEVELOPED)

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: I Facilitv ID: 800074 Revision#: 28 Date: January 14.2015 

## FACILITYPERMITTOOPERATE LACITY, DWPHAYNES GENERATING STATION SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywith the terms and conditions setforth below: Equipment

System.I: 

### BQ1LERS BOILER, UNIT NO. I, FUEL OIL, NATURAL GAS, COMBUSTION ENGINEERING, FRONT FIRED. AIR PREHEATED, WITH OXYGEN CONTENT CONTROL, 2240 MMBTU/HR WITH A/N: 410730

GENERATOR, 230 MW INJECTOR, MAGNESIUM COMPOUNDS, FUEL OIL ADDITIVE SYSTEM SELECTIVE CATALYTIC REDUCTION, NO. I, TWO BABCOCK & WILCOX REACTORS, WITH 72 FULL MODULES AND 6 HALF MODULES, CATALYST VOLUME 3850 CU. FT., WIDTH: 19 FT 3 !N; HEIGHT: 23 FT 9 IN; LENGTH: 9 FT IOINWITH AIN: 541988
AMMONIA INJECTION, UNIT NO. I, TWO AMMONIA/AIR INJECTION GRIDS, EACH HAVING 1104 INJECTION NOZZLES 

### ID Connected No. To

DI C73 S96

C73 DI

C74 

### RECLAIM Source Type/ Monitoring Unit

NOX: MAJOR SOURCE** Emissions• 

### And Requirements

CO: 2000 PPMV (5) [RULE 407 0 4-2-1982]; i'iOX: 5 PPMV (5A) (RULE 2009, 5·11-2001]; NQX: 12.37 LBS/IOOOGAL FUEL OIL (I) [RULE 2012. S-6-2005); PM: 0.1 GRA!NS/SCF (5) [RULE409, '8-7-1981]; S02: (9) [40CFR 72- Acid Rain Provisions, 11-24-1997); SOX: 500 PPMV FUEL OIL (5) [RllLE 407, 4-2-1982)

NH3: 10 PPMV FUEL OIL (4) [RULE 1303(a)(l)-BACT, S-10-1996; RULE 1303(a)(/) -BACT, 12-6-2002); NH3: 20 PPMV NATURAL GAS (4) (RULE IJOJ(a)(l)-BACT, 5-10-1996; RULE /303(a)(/J -BACT. 12-6-2002]



### • (I) (IA} (18)Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (5A) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit 

### Conditions

Al95.5, B59.!, DI82.I, D371.l, E202.l, E204.I, E204.2, Kl71.l

A99.I, Dl2.2, Dl2.3, D28.3, 0298, E73.I, El79.l, El79.2

(7) Denotes NSR applicability limit (8) (SA) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (9) See App Bfor Emission Limits (10) See section J forNESHAP/MACT requirements ** Refer to section F and Gofthis permit to determine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 2 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LA CITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS Theoperator shallcomplywiththe terms and conditions setforth below: Equipment ID 

### Connected RECLAIM Emissions

### • Conditions No. To SourceType/ And Requirements Monitoring Unit

STACK. BOILER NO. I S96 DI A/N: 410730 BOILER. UNIT NO. 2, FUEL OIL, D4 C75 S97 NOX: MAJOR CO: 2000 PPMV (5) [RULE407, Al95.5, NATURAL GAS. COMBUSTION SOURCE** 4-2-1982); NOX: 5 PPMV (SA) B59.l, ENGINEERING. FRONTFIRING, AIR [RULE 2009, 5-11-2001); NOX: 0182.l. PREHEATED, WITH OXYGEN 12.37 LBS/IOOO GAL FUELOIL 0371.l, CONTENT CONTROL, 2240 (I) [RULE 2012, 5-6-2005); PM: E202.l, MMBTU/HRWITH O. l GRAINS/SCF (5) [RULE 409, E204.l, A/N: 410732 8-7-1981); S02: (9) [40CFR72

- E204.2. Add Rain Provisions, Kl71.l 11-24-1997): SOX: 500PPMV FUELOIL (5) [RULE 407, 4-2-1982)
INJECTOR, MAGNESIUM COMPOUNDS. FUEL OIL ADDlTlVE SYSTEM GENERATOR, 230 MW SELECTIVE CATALYTIC C75 D4 NH3: lO PPMV FUEL OIL (4) A99.l, 012.2, REDUCTION. NO. 2, TWO BABCOCK [RULE 1303(a)(l)-BACT, Dl2.3, 02S.3, & WILCOX REACTORS, WITH 72 5-10-1996; RULE/303(a)(/) 029.S, E73.l, FULL MODULES AND 6 HALF -BACT, 12-6-2002); NH3: 20 E179.1, MODULES. CATALYSTVOLUME PPMV NATURAL GAS (4) El79.2 3S50 CU. FT.• WIDTH: 19 FT 3 IN; [RULE 1303(a)(l)-BACT, HEIGHT: 23 FT 9 IN; LENGTH: 9 FT 5-10-1996; RULE/303(a)(l) IO IN WITH -BACT. 12-6-2002) A/N: 5419S9
AMMONIA INJECTION, UNIT C76 NO. 2, TWOAMMONIA/AIR INJECTION GRIDS, EACH HAVING 1104 INJECTION NOZZLES * (1) (IA) (lB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIMemissionrate (3) Denotes RECLAIM concentrationlimit (4) Denotes BACT emission limit (5) (SA) (SB) Denotes commandand control emission limit (6) Denotes airtoxic control rule limit (7) Denotes NSR applicability limit (S) (SA) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS. etc.) (9) See App B for Emission Limits (I0) See section J for NESHAP/MACT requirements ** Referto section F and G ofthis permit to determine the monitoring, recordkeeping andreporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive. Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page· 3 Facility ID· 800074 Revision#: 28 Date: January 14, 2015



## LACITY, DWPHAYNES GENERATING STATION SECTIOND: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywiththe terms and conditions setforth below: Equipment ID Connected No. To



## • (1) (IA) (IB) Denotes RECLAIMemission factor (3) Denotes RECLAIM concentrationlimit (5) (SA) (58) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits RECLAIM SourceType/ Monitoring Unit Emissions· And Requirements

(2) (2A) (28) Denotes RECLAIM emission rate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit Conditions

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (IO) See section J for NESHAP/MACT requirements •• Refer to section F and G ofthis permitto determine the monitoring, recordkeeping and reportingrequirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 4 Facility JD· 800074 Revision#: 28 Date· January 14, 2015 

## FACILITYPERMITTOOPERATE LA CITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shallcomplywith theterms and conditions set forth below: Equipment ID Connected No. To

GAS TURBINE, UNIT NO. 9, DIESEL FUEL, NATURAL GAS, GENERAL ELECTRIC, MODEL PG724IFA, COMBINED CYCLE, WATER INJECTION (DIESEL FIRING ONLY), WITH LOW NOX BURNER, 1757 MMBTU/HR WITH A/N: 517866

GENERATOR, (MAX GROSS OUTPUT AT 65 DEG. F), 169.9 MW Dl25



### • (1) (lA) (18) Denotes RECLAIMemission factor CI30

(3) Denotes RECLAIM concentration limit (5) (SA) (58) Denotes command and control emission limit (7) Denotes NSRapplicability limit (9) See App B for Emission Limits RECLAIM SourceType/ Monitoring Unit

NOX: MAJOR SOURCE•• Emissions* And Requirements

CO: 4 PPMV (4) [RULE I303(a) (1)-BACT, S-10-19%; RULE l303(a)(l)-BACT, 12-6-2002]; CO: 2000 PPMV (5) [RULE 407, 4-2-1982]; NOX: 2 PPMV NATURAL GAS (4) [RULE 2005, S-6-2005]: NOX: 22.16 LBS/IOOO GAL DIESEL (I) [RULE 2012, S-6-2005]; NOX: 111 PPMV NATURAL GAS (8) [40CFR60 SubpartGG, 3-<H981]; NOX: 121 PPMV DIESEL (8) [40CFR60 Subpart GG,3-6-1981]; PM: 0.01 GRAINS/SCF (SA) [RULE 47S, 10-8-1976; RULE475, 8-7-1978]; PM: 0.1 GRAINS/SCF NATURAL GAS (5) [RULE 409, 8-7-1981]; PM: II LBS/HR (5B) [RULE475, 10-8-1976; RULE 475. 8-7-1978]; S02: (9) [40CFR 72

- Acid Rain Provisions, 11-24-1997]; SOX: 150 PPMV (8) [40CFR 60 SubpartGG, 3-6-1981]; SOX: 500 PPMV FUEL OIL (5) [RULE 407, 4-2-1982];voe: 2 PPMV (4) [RULE 1303(a)(l)-BACT, 5-10-19%; RULE 1303(a)(l) -BACT, 12-6-2002]

(2) (2A) (28) Denotes RECLAIM emission rate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit Conditions

A63.3, A99.2, A99.3, Al95.l, Al95.2, Al95.3, A327.l, A433.I, 875.1, D29.4, D29.5, D82.l, D82.2, D372.I,E57.I, EI93.l, K40.3, K67.4

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See section J for NESHAP/MACT requirements •• Refer to section Fand G ofthis permit to determine the monitoring. recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar. CA 91765-4178 Section D facility ID Revision#: Page: 5 800074 28 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LA CITY, DWPHAYNES GENERATING STATION SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywith the terms and conditions set forth below: Equipment ID Connected No. To

GENERATOR, HEAT RECOVERY STEAM
STEAM TURBINE, STEAM, UNIT NO. 8, COMMONTOGAS TURBINES NO. 9 ANDNO. IO, 257 MW (AT 65 DEG. F) BURNER, DUCT, NATURAL GAS, LOCATED IN THE HRSG OF TURBINE NO. 9, 286.6MMBTU/HR A/N: 517866 0129



### • (I) (IA)(IB) Denotes RECLAIM emission factor CI30

(3) Denotes RECLAIM concentration limit (5) (SA) (5B) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits RECLAIM Source Type/ Monitoring Unit

NOX:MAJOR SOURCE** Emissions• And Requirements

CO: 4 PPMV (4) [RULE IJOJ(a) (l)-BACT,5-10-1996; RULE I 303(a}(l)-BACT. I2-6-2002]; CO: 2000 PPMV (5) [RULE 407, 4-2-1982]; NOX: 0.2 LBS/MMBTU NATURAL GAS (8) [40CFR 60Subp8'tDa, 10-4-1991]; NOX: 2 PPMV NATURAL GAS (4) [Rlll.E 2005, 5-6-2005]; PM: O.ot GRAINS/SCF (5A) [RULE 475, 10-8-1976; RULE 475, 8-7-1978]; PM: 0.03 LBS/MMBTU NATURAL GAS (8) (40CFR 60 SubpartDa, 10-4-1991]; PM: 0.1 GRAINS/SCF NATURAL GAS (5)[RULE409, 8-7-1981]; PM: 11 LBS/HR (5B) [RULE 475, 10-8-1976; RULE 475, 8-7-1978]; S02: (9) [40CFR 72

- Acid Rain Provisions, 11-24-1997); SOX: 0.2 LBS/MMBTU NATURAL GAS (8) [40CFR 60 SubpartDa, 10-4-1991];voe: 2 PPMV (4) [RULE IJOJ(a)(l)-BACT, 5-10-1996; RULE 1303(a}(l) -BACT. I2-6-2002] (2) (2A) (28) Denotes RECLAIM emission rate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit Conditions

A63.3,A99.2, A99.3, Al95.I, Al95.2, Al95.3, A327.I, A433.I, B75.I, 029.4, 029.5, 082.I, D82.2, D372.1,E57.I, El93.I, K40.3, K67.4

(8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (I0) See section J for NESHAP/MACT requirements •• Refer to section Fand G ofthis permit to determine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-41 78 Section D Page: 6 Facility ID: 800074 Revision#: 28 Date· January 14. 2015 

## FACILITYPERMITTO OPERATE LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operatorshall complywiththe terms and conditions set forth below: Equipment

COOXIDATION CATALYST, SERVING UNIT NO. 9, HITACHI, MITSUBISHI, PEERLESS OR EQUAL, HEIGHT:61 FT; LENGTH:26 FT; WIDTH:4 FT; WITH 6344 CUBIC FEET OF CATALYST VOLUME A/N: 432467 SELECTIVE CATALYTIC REDUCTION, SERVING UNIT NO. 9, HITACHI, MITSUBISHI, PEERLESS OREQUAL, HEIGHT: 61 FT; LENGTH:26 FT; WIDTH: 5 FT, WITH 7930 CU FEET OF CATALYST VOLUME WITH A/N: 432467
AMMONIA INJECTION, INJECTION GRID STACK, SERVING UNIT NO. 9, HEIGHT: 140 FT; DIAMETER: 19 FT A/N: 517866 ID No.

CI30

Cl31

SI33



### • (I) (IA) (IB) Denotes RECLAIM emission factor Connected To

0125 Dl29 Cl31

CI30 SI33

Cl31

(3) Denotes RECLAIM concentration limit (5) (SA) (5B) Denotes command andcontrol emission limit (7) Denotes NSR applicability limit (9) See App B forEmission Limits RECLAIM SourceType/ Monitoring Unit Emissions

### • And Requirements

NHJ: 5 PPMVNATURAL GAS (4) [RULE 1303(a)(l)-BACT, 5-10-1996; RULE/303(a)(/) -BACT, 12-6-2002)

(2) (2A) (2B) Denotes RECLAIM emissionrate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit Conditions

Al95.4, 012.6, 012.7, 012.8, 029.2, E73.2, El79.3, El79.4

(8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (I0) See sectionJ for NESHAP/MACT requirements • • Referto section F and G ofthis permit to detennine the monitoring, recordk.eeping andreporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 7 Facilitv ID: 800074 Revision#' 28 Date: January 14,2015 

## FACILITYPERMITTOOPERATE LA CITY, DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFICCONDITIONS The operator shall comply withthe terms and conditions set forth below: Equipment

GAS TURBINE, UNIT NO IO, DIESEL FUEL, NATURAL GAS, GENERAL ELECTRIC, MODEL PG724IFA, COMBINED CYCLE,WATER INJECTION (DIESEL FIRING ONLY), wmI LOW NOX BURNER, I757 MMBTUIHRWITH A/N: 518035

GENERATOR, (MAX GROSS OUTPUT AT 65 DEG. F), 169.9 MW 

### ID Connected No. To



### • (I) (IA) (IB) Denotes RECLAIM emission factor (3) Denotes RECLAIM concentration limit (5) (SA) (SB) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits 

### RECLAIM Source Type/

NOX: MAJOR SOURCE** Emissions* 

### And Requirements

CO: 4 PPMV (4) [RULE IJOJ(a) (l}-BACT,5-10-1996; RULE /303(a)(/)-BACT. I2-6-2002]; CO: 2000 PPMV (5) (RULE 407, 4-2-1982]; NOX: 2 PPMV NATURAL GAS (4) [RULE 2005, 5-6-2005]: NOX: 22.16 LBS/IOOO GAL DIESEL (I) [RULE 2012,5-6-2005]:NOX: I I I PPMV NATURAL GAS (8) [40CFR68SubpartGG, J-6-1981]; NOX: 121 PPMV DIESEL (8) [40CFR 60Subpart GG,J-li-1981]: PM: 0.01 GRAINS/SCF (SA) [RULE 475, 10-8-1976; RULE475, 8-7-1978]; PM: 0.1 GRAINS/SCF NATURAL GAS (5) [RULE 409, 8-7-1981]: PM: I I LBS/HR (SB) [RULE475, 10-8-1976; RULE 475, 8-7-1978]: S02: (9) [40CFR 72 -Acid Rain Provisions. 11-24-1997]: SOX: 150 PPMV (8) [40CFR 60 SubpartGG, J-6-1981]: SOX: 500 PPMV FUEL OIL (5) [RULE 407, 4-2-1982]: voe 2 PPMV (4) [RULE IJOJ(a)(l}-BACT, 5-10-1996; RULE 1303(a)(/) -BACT, 12-6-2002]

(2)(2A) (28) Denotes RECLAIM emission rate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit 

### Conditions

A63.2, A99.2, A99.3, Al95.I, Al95.2, AI95.3, A327.I, A433.I, B75.I, D29.4, 029.5, D82.I, D82.2. 0372.I, E57.I, El93.I, K40.3, K67.4

(8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See section J for NESHAP/MACT requirements •• Refer to section F and G ofthis permit to determine the monitoring, recordkeeping and reporting requiremen.ts for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 8 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTO OPERATE LACITY,DWPHAYNES GENERATING STATION SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS Theoperatorshallcomplywith theterms and conditions set forth below: Equipment ID Connected RECLAIM Emissions• Conditions No. To Source Type/ And Requirements Monitoring Unit

### ~roe~···roWINEl::t:YCtilfc&t\S'tlRB:tl'@l6EN'···'rl<Wt¥.**tar·····~··**

# ...**~** ••• :. • •h

. . •• ..•• • ..•., • .... . • . '

. 

### F;. .•**.~** 

# s'
...... . GENERATOR, HEAT RECOVERY STEAM
STEAM TURBINE, STEAM, UNIT NO. 8, COMMON TO GAS TURBINES NO. 9 AND NO. IO, 257 MW (AT 65 DEG. F) BURNER, DUCT, NATURAL GAS, Dl42 Cl38 NOX: MAJOR CO: 4 PPMV (4) (RULE 130J(a) A63.2, A99.2, LOCATED IN THE HRSG OF SOURCE*• (l)-BACT,5-10-1996; RULE A99.3, TURBINE NO. 10, 286.6 MMBTU/HR 1303(a){/)-8ACT, I2-6-2002]; Al95.I, A/N: 518035 CO: 2000 PPMV (5) [RULE 407, Al95.2, 4-2-1982]; NOX: 0.2 Al95.3, LBS/MMBTU NATURAL GAS A327.I, (8) (40CFR60Subpart Da, A433.I, 10-4-1991]; NOX: 2 PPMV B75.I, D29.4, NATURAL GAS (4) [RULE 029.5' D82. I, 2005, 5-6-2005]; PM: 0.01 D82.2, GRAINS/SCF (5A) [RULE 475, D372.l,E57.I, 10-8-1976; RULE 475, 8-7-1978]; E193.I, K40.3, PM: 0.03 LBS/MMBTU K67.4 NATURAL GAS (8) (40CFR 60 Subpart Da, 10-4-1991]; PM: 0.1 GRAINS/SCF NATURAL GAS (5)[RULE 409, 8-7-1981]; PM: II LBS/HR (5B) (RULE475, 10-8-1976; RULE475, 8-7-1978]; S02: (9) (40CFR72

- Add aa;n Provisions, 11-24-1997): SOX: 0.2 LBS/MMBTU NATURAL GAS (8) (40CFR 60 Subpart Da, 10-4-1991];voe: 2 PPMV (4) (RULE IJOJ(a)(l)-BACT, 5-10-1996; RULE 1303(a)(/) -BACT, 12-6-2002] 

## • (I) (IA) (IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emissionrate (3) Denotes RECLAIM concentration limit (4) Denotes 8ACTemission limit (5) (5A) (58) Denotes command and control emission limit (6) Denotes airtoxic control rule limit (7) Denotes NSR applicability limit (8) (SA) (88) Denotes 40CFR limit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (I0) See section J for NESHAPIMACT requirements •• Refer to section F and G ofthis permit to determine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Faci1itv ID: Revision#: Page: 9 800074 28 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY, DWPHAYNES GENERATING STATION SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFICCONDITIONS The operator shall complywith theterms and conditions set forth below: Equipment ID 

### Connected RECLAIM Emissions• 

### Conditions No. To SourceType/ And Requirements Monitoring Unit**yfroceSS)~:** 

### ····

### ~~:cv<:g;GAS~INEGEN~~TJf),j11$YS~:

## ~· CO OXIDATION CATALYST, Cl38 Dl34Cl39 SERVING UNIT NO. 10, HITACHI, Dl42 MITSUBISHI, PEERLESS OR EQUAL, HEIGHT:61 FT: LENGTH:26 FT; WIDTH:4 FT: WITH 6344 CUBIC FEET OF CATALYST VOLUME A/N: 432466 SELECTIVE CATALYTIC Cl39 Cl38 Sl41 NHJ: 5 PPMV NATURAL GAS Al95.4, REDUCTION, SERVING UNIT NO. I0, (4) IRULE 1303(•)(1)-BACT, Dl2.6, Dl2.7, HEIGHT: 61 FT: LENGTH:26 FT: 5-10-1996; RULE J303(a)(I) Dl2.8, D29.2, WIDTH: 5 FT, WITH 7930 CU FEET -BACT, I2-6-2002) E73.2, El79.3, OF CATALYST VOLUME WITH E179.4 A/N·. 432466
AMMONIA INJECTION, INJECTION GRID STACK, SERVING UNIT NO. 10, Sl41 Cl39 HEIGHT: 140 FT; DIAMETER: 19 FT A/N: 518035 

## 'Proc
.. 

## 31 StliPLE't'.VCLE**~..\tS '1'1J'Rij1NE1'9WER'~.ENE~1't'ON'~TE~tl•".'.**  .';'<"'Si;



### • (I) (IA) (IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emissionrate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (SA) (SB) Denotes command and control emission limit (6) Denotes air toxic control rule limit (7) Denotes NSR applicability limit (8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (10) See section J for NESHAP!MACT requirements •• Refer to section F and G ofthis pennit to detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 10 Facilitv ID 800074 Revision#: 28 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY,DWPHAYNES GENERATING STATION SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operatorshall comply withthe terms and conditions set forth below: Equipment ID Connected RECLAIM Emissions

### • Conditions No. To SourceType/ And Requirements Monitoring Unit**lff~~ij'J;;** 

## SI ·-**-'E'd~Lt·•:TV).ijjlm; lt~~~ON'~f:if'.-~**  GAS TURBINE, UNIT 11, NATURAL 0159 Cl61 NOX: MAJOR CO: 4 PPMV (4) (RULE 1703- A63.4, A99.6, GAS, GENERAL ELECTRIC, MODEL SOURCE** PSDAnalysis. 10-7-1988}; CO: Al95.8, LMSIOOPA, INTERCOOLED, WITH 2000 PPMV (5) (RULE 407. A195.9, WATER INJECTION, WITH WATER 4-2-1982]; NOX: 2.5 PPMY (4) A195. IO, INJECTION, 906.6 MMBTU/HR (RULE 1703

- PSD Analysis, A327. I, Ci.4, WITH I0-7-1988; RULE 2005. Cl.5, 029.7, AIN: 559600 5-6-2005]: NOX: 25 PPMV (8) 082.3, 082.4, (40CFR 60 Subpart KKKK. E193.6, 7+2006]: PM: 0.01 E193.7, GRAINS/SCF (SA) (RULE 475, El93.10, I0-8-1976; RULE475, 8-7-1978]: K67.6 PM: 0.1 GRAINS/SCF (5) [RULE 409,8-7-I981];PM: II LBS/HR (SB) [RULE 475, 10-8-1976; RULE475, 8-7-1978]: PMIO: 5.8 LBS/HR (4) [RULE IJOJ(b)(2) -Offset, 5-10-1996; RULE/303(b) (2)-0jfsel. 12-6-2002]; S02: (9) (40CFR 72

- Atid Rain Provisions., 11-24-1997]; 502: 0.9 LBS/MEGAWATT-HOUR (8A) [40CFR60Subpart KKKK. 7-6-2006];voe: 2 PPMV (4) (RULE IJOJ(a)(l)-BACT, 5-10-1996; RULE/303(a)(I) -BACT, I2-6-2002]
GENERATOR, GROSS AT65 F, I02.7MW

• (1) (IA) (lB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emissionrate (3) Denotes RECLAIM concentration Jimit (4) Denotes 8ACT emission 1imit (5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit (7) Denotes NSR applicability limit (8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (I0) See section J for NESHAP/MACT requirements •• Refer to section Fand G ofthis permit to detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page 11 Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY, DWP HAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywith the terms and conditions set forth below: Equipment ID 

### Connected RECLAIM Emissions• 

### Conditions No. To SourceType/ And Requirements Monitoring Unit

### :Pro~!Ji·**S9LE~1€LE'~T~EPID\IER~~'fl().N[~STE~f;Wt!···** 

## "'''?!''·
. COOXIDATION CATALYST, BASF, Cl61 Dl59Cl62 SS FOIL WITH ALUMINA WASHCOAT, MODEL CAMET, 80 MODULES, CATALYSTTOTAL VOLUME: 160 CUBIC FEET AIN:495978 SELECTIVE CATALYTIC Cl62 Cl61 Sl64 NHJ: 5 PPMV (4) [RULE IJOJ(a) Dl2.9, REDUCTION, CORMETECH, MODEL: (1)-BACT, 5-10-1996; RULE Dl2.IO, CMHT-27, WITH 12 MODULES, 1211 /303(a)(l)-BACT: 12-6-2002] Dl2.ll, CU.FT WITH D29.8, El79.5, A/N: 495978 El79.6, E193.9
AMMONIA INJECTION 

## I STACK, SERVING UNIT 11, HEIGHT: Sl64 Cl62 150 FT: DIAMETER: 13 FT 6 IN A/N: 559600



### • (I) (IA) (18)Denotes RECLAIM emission factor (2) (2A) (2B) Denotes RECLAIM emission rate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (5A) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit (7) Denotes NSR applicability limit (8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (9) SeeApp B For Emission Limits (10) See section J for NESHAP/MACTrequirements •• Refer to section F and G ofthis pennitto detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 12 Facility ID: 800074 Revision#: 28 Date· January 14, 2015 

## FACILITYPERMITTOOPERATE LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS Theoperatorshallcomply with the terms and conditions set forth below: Equipment ID Connected 

### No. To

GAS TURBINE, UNIT 12, NATURAL GAS, GENERAL ELECTRIC, MODEL LMSIOOPA, INTER COOLED, WITH WATER INJECTION, WITHWATER INJECTION, 906.6 MMBTU/HR WITH A/N: 559601

GENERATOR, GROSS AT 65 F, !02.7MW Dl65



### • (I) (IA) (IB) Denotes RECLAIM emission factor Cl67

(3) Denotes RECLAIM concentration limit (5) (SA) (58) Denotes commandand control emissionlimit (7) Denotes NSR applicability limit (9) See App B for EmissionLimits RECLAIM SourceType/ Monitoring Unit

NOX: MAJOR SOURCE** Emissions• And Requirements

CO: 4 PPMVNATURAL GAS (4) [RULE 1703- PSD Analysis, 10-7-1988]; CO: 2000 PPMV (5) (RULE407, 4-2-1982]; NOX: 2.5 PPMVNATURAL GAS (4) [RULE 1703

- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005]; NOX: 25 PPMV NATURAL GAS (8) (40CFR 60 Subpart KKKK,7-6-2006]; PM: 0.01 GRAINS/SCFNATURAL GAS (SA) )RULE 475, 10-8-1976; RULE475, 8-7-1978]; PM: 0.1 GRAINS/SCF NATURAL GAS (5) (RULE 409, 8-7-1981]: PM: 11 LBS/HRNATURAL GAS (58) (RULE 475, 10-8-1976; RULE 475. 8-7-1978]; PMlO: 5.8 LBS/HR (4) (RULE 1303(b)(2) -Offset,5-10-1996; RULE l303(b) (2)-0ffset. 12-6-2002]; S02: (9) [ 40CFR72

- Acid Rain Provisions, 11-24-1997]; S02: 0.9 LBS/MEGAWATT-HOUR NATURAL GAS (8A) [40CFR 60 Subpart KKKK, 7-6-2006]; voe: 2 PPMVNATURAL GAS (4) [RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l) -BACT. 12-6-2002]

(2) (2A) (28) Denotes RECLAIM emissionrate (4) Denotes BACT emission liinit (6) Denotes airtoxic control rule limit Conditions

A63.4, A99.6, Al95.8, Al95.9, Al95. IO, A327. I,Cl.4, Cl.5, 029.7, 082.3, 082.4, E193.6, El93.7, El93. 10, K67.6

(8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See section J for NESHAP/MACT requirements •• Refer to sectionF and G ofthis permit to detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 13 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LACITY, DWP HAYNES GENERATINGSTATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywiththe terms and conditions setforth below: Equipment

CO OXIDATION CATALYST, BASF, SS FOIL WITH ALUMINA WASHCOAT, MODEL CAMET, 80 MODULES, CATALYST TOTAL VOLUME: 160 CUBICFEET A/N: 495980 SELECTIVE CATALYTIC REDUCTION, CORMETECH, MODEL: CMHT-27, WITH I2 MODULES, I2I I CU.FT. WITH AIN:495980

AMMONIA INJECTION STACK, SERVING UNIT I2, HEIGHT: 150 FT; DIAMETER: I3FT 6 lN AIN: 55960I ID 

### No.

C167

C168

SI70

(I) (IA) (18) Denotes RECLAIM emission factor 

### Connected To

Dl65 CI68

CI67 SI70

CI68

(3) Denotes RECLAIM concentration limit (5) (SA) (58) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits 

### RECLAIM Source Type/ Monitoring Unit Emissions• And Requirements

NH3: 5 PPMV (4) [RULE 1303(a) (1)-BACT, 5-10-1996; RULE /303(a)(/)-BACT, 12-6-2002]

(2) (2A) (28) Denotes RECLAIM emission rate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit 

### Conditions

DI2.9, DI2.IO, DI2.II, 029.8, EI79.5, EI79.6, EI93.9

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See sectionJ for NESHAP/MACTrequirements ** Referto section F and G ofthis permit to determine the monitoring, recordkeeping andreportingrequirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-41 78 Section D Page: 14 Facilitv lD: 800074 Revision#: 28 Date: January 14,2015 

## FACILITYPERMITTOOPERATE LACITY,DWPHAYNES GENERATING STATION SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operatorshall complywith theterms and conditions set forth below: Equipment ID Connected RECLAIM Emissions• Conditions No. To SourceType/ And Requirements Monitoring Unit

### l''J'~'tL

## ···s-1)E"Ol~LEG'.\l~'l'~P~~,~~N'•11i:t~lll'' , 'Li;sf<;,: "'" GAS TURBINE, UNIT 13, NATURAL Dl71 Cl73 NOX:MAJOR CO: 4 PPMV NATURAL GAS A63.4, A99.6, GAS, GENERAL ELECTRIC, MODEL SOURCE** (4)[RULE 1703

- PSD Analysis, Al9S.S, LMSIOOPA, INTERCOOLED, WITH 10-7-1988];CO: 2000 PPMV (S) Al9S.9, WATER INJECTION, WITH WATER [RULE407,4-2-1982]; NOX: 2.S Al9S.l0, INJECTION, 906.6 MMBTU/HR PPMV NATURAL GAS (4) A327. l, Cl.4, WITH [RULE 1703

- PSD Analysis. Cl.5, 029.7, A/N: SS9602 10-7-1988; RULE 2005. DS2.3. DS2.4, 5-6-2005]; NOX: 2S PPMV E193.6, NATURAL GAS (S) [40CFR60 El93.7, Subpart KKKK,7-6-2006]; PM: El93.IO, 0.01 GRAINSISCF NATURAL K67.6 GAS (SA) [RULE 475. 10-8-1976; RULE475, 8-7-1978]; PM: 0.1 GRAINSISCF NATURAL GAS (S)(RULE409,8-7-!98l]iPM: II LBS/HRNATURAL GAS (SB) [RULE 475. 10-8-1976; RULE 475. 8-7-1978]; PMIO: 5.S LBS/HR (4) [RULE IJOJ(b)(2) -Offs<t,5-I0-1996; RULE/303(b) (2)-0ffset. 11-6-2002); 502: (9) [40CFR72

- Acid Rain Provisions.11-24-1997]; S02: 0.9 LBS/MEGAWATT-HOUR NATURAL GAS (SA) [40CFR 60 SubpartKKKK,7-6-2006]; voe: 2 PPMV NATURAL GAS (4) [RULE IJOJ(a)(l)-BACT, 5-ltH996; RULE/303(a)(I) -BACT, 12-6-2002)
GENERATOR, GROSS AT 6S F, 102.7MW



### • (I) (IA)(18) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAlM emissionrate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (SA) (58) Denotes command and control emission limit (6) Denotes airtoxic control rule limit (7) Denotes NSR applicability limit (S) (SA) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (10) See section J for NESl-lAP/MACT requirements •• Referto section Fand G ofthis pennit to detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Facilitv ID: Revision#: Page: 15 800074 28 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY, DWP HAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywiththeterms and conditions set forth below: Equipment

CO OXIDATION CATALYST, BASF, SS FOIL WITH ALUMINA WASHCOAT, MODEL CAMET, 80 MODULES, CATALYST TOTAL VOLUME: 160 CUBICFEET AIN: 495988 SELECTIVE CATALYTIC REDUCTION, CORMETECH, MODEL: CMHT-27, WITH 12 MODULES, 1211 CU.FT. WITH AIN:495988

AMMONIA INJECTION STACK, SERVING UNIT 13, HEIGHT: 150 FT ; DIAMETER: 13 FT 6 IN AIN: 559602 ID 

### No.

Cl73

Cl74

Sl76



### • (1) (IA) (lB) Denotes RECLAIM emission factor 

### Connected To

Dl71 Cl74

Cl73 Sl76

Cl74

(3) Denotes RECLAIM concentrationlimit (5) (5A) (5B) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits 

### RECLAIM SourceType/ Monitoring Unit Emissions• And Requirements

NH3: 5PPMV (4) [RULE 1303(a) (1)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002]

(2) (2A) (28) DenotesRECLAIM emission rate (4) Denotes BACT emissionlimit (6) Denotes air toxic control rule limit 

### Conditions

Dl2.9, Dl2.IO, Dl2.ll, D29.8, E179.5, El79.6, El93.9

(8) (SA) (80) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See sectionJ for NESHAP/MACTrequirements •• Refer to section F and G ofthis pennit to determine the monitoring, recordkeeping andreporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page· 16 Facilitv ID· 800074 Revision#: 28 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywiththeterms and conditions set forth below: Equipment

GAS TURBINE, UNIT 14, NATURAL GAS, GENERAL ELECTRIC, MODEL LMSIOOPA, INTERCOOLED, WITH WATER INJECTION, WITH WATER INJECTION, 906.6 MMBTU/HR WITH A/N: 559603

GENERATOR. GROSS AT 65 F, 102.7MW ID No.

0177



## • (I) (IA) (IB) DenotesRECLAIM emission factor 

### Connected To

CI79

(3) Denotes RECLAIM concentration limit (5) (5A) (5B) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits 

### RECLAIM SourceType/ Monitoring Unit

NOX:MAJOR SOURCE** Emissions* 

### And Requirements

CO: 4 PPMVNATURAL GAS (4) [RULE 1703- PSD Analysis, 10-7-1988]; CO: 2000 PPMV (5) [RULE 407, 4-2-1982]; NOX: 2.5 PPMV NATURAL GAS (4) [RULE 1703

- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005]; NOX: 25 PPMV NATURAL GAS (8) [40CFR60 SubpartKKKK,7-6-2006]; PM: 0.01 GRAINS/SCF NATURAL GAS (SA) [RULE 475, 10-8-1976; RULE475. 8-7-1978]: PM: 0.1 GRAINS/SCF NATURAL GAS (S)[RULE 409, 8-7-1981]: PM: 11 LBS/HR NATURAL GAS (SB) [RULE 475, 10-8-1976; RULE 475, 8-7-1978]; PMIO: 5.8 LBS/HR (4) [RULE 1303(b)(2) -Offset,S-10-1996; RULE /303(b) (2)-0.ffset. 12-6-2002]: S02: (9) [40CFR 72

- Acid Rain Provisions, 11-24-1997]; S02: 0.9 LBS/MEGAWATT-HOUR NATURAL GAS (8A) [40CFR 60 Subpart KKKK, 7-6-2006]: voe: 2 PPMV NATURAL GAS (4) [RULE 1303(a)(l)-BACT, 5-10-1996; RULE/303(a}(1} -BACT, 12-6-2002]

(2) (2A) (2B) Denotes RECLAIM emissionrate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit 

### Conditions

A63.4, A99.6, Al95.8, Al95.9, Al95.IO, A327.l,Cl.4, Cl.5, 029.7, 082.3, 082.4, El93.6, El93.7, EI93. IO, K67.6

(8) (8A) (88) Denotes40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See sectionJ for NESHAP/MACT requirements •• Refer to sectionF and G ofthis permitto determine the monitoring, recordk.eeping and reportingrequirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar. CA 91765-4178 Section D Page· 1 7 Facility ID: 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LACITY, DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywith theterms and conditions set forth below: Equipment

CO OXIDATION CATALYST, BASF, SS FOIL WITH ALUMINA WASHCOAT, MODEL CAMET, 80 MODULES, CATALYST TOTAL VOLUME: 160 CUBIC FEET A/N: 495989 SELECTIVE CATALYTIC REDUCTION, CORMETECH, MODEL: CMHT-27, WITH 12 MODULES, 1211 CU.FT. WITH A/N: 495989

AMMONIA INJECTION STACK, SERVING UNIT 14, HEIGHT: 150 FT : DIAMETER: 13 FT 6 IN A/N: 559603 ID 

### No.

Cl79

Cl80

Sl82



### • (I) (IA) (IB)Denotes RECLAIM emission factor 

### Connected To

Dl77 Cl80

CI79Sl82

Cl80

(3) Denotes RECLAIM concentration limit (5) (5A) (58) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits 

### RECLAIM SourceType/

Monitoring Unit Emissions * 

### AndRequirements

NHJ: 5 PPMV (4) [RULE 1303(a) (1)-BACT, S-J0-1996; RULE 1303(a)(J)-BACT, 12-6-2002]

(2) (2A) (28) Denotes RECLAIM emissionrate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit 

### Conditions

Dl2.9, Dl2.l0, 012.11, 029.8,El79.5, El79.6, E193.9

(8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (IO) See section J for NESHAP/MACTrequirements ** Refer to sectionF and G ofthis pennit to detennine the monitoring, record.keeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 9t765-41 78 Section D Facilitv ID: Revision#: Page: Ti 800074 28 Date: January 14. 2015 

## FACILITYPERMITTO OPERATE LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS Theoperatorshallcomplywith theterms and conditions set forth below: Equipment ID Connected No. To

GAS TURBINE, UNIT 15, NATURAL GAS, GENERAL ELECTRIC, MODEL LMSIOOPA, INTERCOOLED, WITH WATER INJECTION, WITH WATER INJECTION, 906.6 MMBTU/HR WITH A/N: 559604

GENERATOR, GROSS AT 65 F, I02.7MW Dl83



## • (I) (IA)(18) Denotes RECLAIM emission factor CI85

(3) Denotes RECLAIM concentration limit (5) (5A) (58) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits RECLAIM SourceType/ Monitoring Unit l NOX:MAJOR SOURCE** Emissions· And Requirements

CO: 4 PPMV NATURAL GAS (4) [RULE 1703 • PSD Analys;s, 10-7-1988]; CO: 2000 PPMV (5) [RULE 407, 4--2-1982]; NOX: 2.5 PPMVNATURAL GAS (4) [RULE 1703

- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005]; NOX: 25 PPMV NATURAL GAS (8) [40CFR60 Subpart KKKK., 7-6-2006); PM: 0.01 GRAINS/SCF NATURAL GAS (SA) [RULE475, 10-8-1976; RULE475, 8-7-1978); PM: 0.1 GRAINS/SCF NATURAL GAS (5) [RULE 409, 8-7-1981]; PM: 11 LBS/HR NATURAL GAS (58) [RULE 475, 10-8-1976; RULE 475, 8-7-1978]; PMIO: 5.8 LBS/HR (4) [RULE 1303(b)(2) -Offset,5-10-1996; RULE/ 303(b) (2)-0ffeet, 12-6-2002]; S02: (9) [40CFR 72

- Acid Rain Provisions, t 1-24-1997]; S02: 0.9LBS/MEGAWATT-HOUR NATURAL GAS (8A) [40CFR 60 Subpart KKKK,7-6-2006]; 

### voe: 2 PPMVNATURAL GAS (4) [RULE 1303(a)(l)-BACT, 5-10-1996; RULE/303(a)(l) -BACT. 12-6-2002]

(2) (2A) (2B) Denotes RECLAIM emissionrate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit Conditions

A63.4, A99.6, Al95.8, Al95.9, AI95. IO, A327. I, Cl.4, Cl.5, 029.7, D82.3, D82.4, El93.6, El93.7, El93.IO, K67.6

(8) (8A) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (I0) See section J for NESHAP/MACTrequirements •• Refer to section F and G ofthis pennit to determine the monitoring, recordkeeping and reporting requirements for this device.

## South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 19 Facility ID: 800074 Revision#: 28 Date· January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY, DWPHAYNES GENERATINGSTATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFICCONDITIONS The operator shall complywith theterms and conditions set forth below: Equipment ID Connected No. To RECLAIM SourceType/ Monitoring Unit Emissions· And Requirements**b7'~SSCT£3=7""'7'7'"'"""2"3'DE3'B'3'8cirr917'l1111E;min,,,,,~"'7""7""7"'1m,_"""**

## il~r:~~~j--~-~--•1Mif,•1::. CO OXIDATION CATALYST, BASF, SS FOIL WITH ALUMINA WASHCOAT, MODEL CAMET, 80 MODULES, CATALYST TOTAL VOLUME: 160 CUBICFEET A/N:495990 SELECTIVE CATALYTIC REDUCTION, CORMETECH, MODEL: CMHT-27, WITH 12 MODULES, 121 I CU.FT WITH A/N: 495990

AMMONIA INJECTION STACK, SERVING UNIT I5, HEIGHT: 150 FT; DIAMETER: 13 FT 6 IN A/N: 559604 Cl85

Cl86

Sl88



### • (I) (IA) (IB) Denotes RECLAIM emission factor Dl83 CI86

Cl85 SI88

Cl86

(3) Denotes RECLAIM concentration limit (5) (SA) (58) Denotes command and control emission limit NHJ: 5 PPMV (4) [RULE 1303(a) (1)-BACT, 5-I0-1996; RULE /303(a)(l)-BACT. 12-6-2002(

(2) (2A) (2B) Denotes RECLAIM emission rate (4) Denotes BACTemissionlimit (6) Denotes air toxic control rule limit 

### Conditions

DI2.9, DI2.IO, DI2.II, D29.8, El79.5, EI79.6, EI93.9

(7) (9) Denotes NSR applicability limit See App B for EmissionLimits (8) (8A) (88) Donotes 40 CFRlimit (e.g. NSPS, NESHAPS, etc.) (I0) See sectionJ for NESHAP/MACT requirements •• Refer to sectionF and G ofthis permitto determine the monitoring, recordk.eeping andreporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 20 Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015 

## FACILITYPERMITTO OPERATE LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS Theoperatorshallcomplywith theterms and conditions set forth below: Equipment ID Connected No. To

GAS TURBINE, UNIT 16, NATURAL GAS, GENERAL ELECTRIC, MODEL LMSlOOPA, INTERCOOLED, WITH WATER INJECTION, WITH WATER INJECTION, 906.6 MMBTUIHR WITH A/N: SS960S

GENERA TOR, GROSS AT 6S F, 102.7MW DIS9



### • (1) (IA) (IB) Denotes RECLAIM emission factor Cl91

(3) Denotes RECLAIM concentration limit (5) (5A) (58) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits RECLAIM SourceType/ Monitoring Unit

NOX:MAJOR SOURCE•• Emissions· And Requirements

CO: 4 PPMVNATURAL GAS (4) [RULE 1703- PSD Analysis, I0-7-19SS]; CO: 2000 PPMV (S) [RULE 407, 4-2·1982]; NOX: 2.5 PPMV NATURAL GAS (4) [RULE 1703

- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005]; NOX: 2S PPMV NATURAL GAS (S) [40CFR60 Subpart KKKK, 7-6-2006]; PM: 0.01 GRAINS/SCF NATURAL GAS (SA) [RULE 475, 10-8-1976; RULE475. 8-7-1978]; PM: 0.1 GRAINS/SCF NATURAL GAS (S)[RULE409, S-7-1981]; PM: II LBS/HR NATURAL GAS (SB) [RULE 475, 10-8-1976; RULE 475, 8-7-1978]; PMJO: 5.S LBS/HR (4) [RULE 1303(b)(2) -Offset, 5-10-1996; RULE1303(b) (2)-0jfset. 12-6-2002]; S02: (9) [40CFR72

- Acid Rain Provisions, 11-24-1997]; S02: 0.9 LBS/MEGAWATT-HOUR NATURAL GAS (SA) [40CFR 60Subp3'1KKKK.7-6-2006]; voe: 2 PPMV NATURAL GAS (4) [RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(I) -BACT, 12-6-2002]

(2) (2A) (2B) Denotes RECLAIM emissionrate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit Conditions

A63.4, A99.6, Al9S.S, Al9S.9, Al9S. l0, AJ27. I, Cl.4, Cl.5, 029.7, OS2.3, OS2.4, EI93.6, El93.7, El93.ID, K67.6

(S) (SA) (SB) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See sectionJ for NESHAP/MACT requirements •• Refer to section F and G ofthis pennit to detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Facilitv ID: Revision#: Page· 21 800074 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LACITY,DWP HAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywith theterms and conditions set forth below: Equipment ID 

### Connected RECLAIM Emissions

# . Conditions No. To SourceType/ And Requirements Monitoring Unit

CO OXIDATION CATALYST, BASF, Cl91 D189Cl92 SS FOIL WITH ALUMINA WASHCOAT, MODEL CAMET, 80 MODULES, CATALYST TOTAL VOLUME: 16-0 CUBIC FEET A/N:495991 SELECTIVE CATALYTIC Cl92 Cl91 Sl94 NHJ: 5 PPMV (4) [RULE IJOJ(a) Dl2.9, REDUCTION, CORMETECH, MODEL: (l)·BACT,5-I0-1996; RULE Dl2.IO, CMHT-27, WITH 12 MODULES, 121 I /303(a)(l)-BACT, 12-6-2002] Dl2.ll, CU.FT. WITH 029.8, El79.5, A/N:495991 E179.6, El93.9
AMMONIA INJECTION STACK, SERVING UNIT 16, HEIGHT: Sl94 Cl92 150 FT: DIAMETER: 13 FT 6 IN A/N: 5596-05

INTERNAL COMBUSTION ENGINE, D53 NOX: PROCESS NOX: 469 LBS/IOOO GAL B59.3, Cl.3, EMERGENCY POWER, DIESEL FUEL, UNIT** DIESEL (I) [RULE 2012, Cl77.I, ALCO, MODEL 251, 16 CYLINDERS, 5-ll-2001; RULE 2012, Dl2.5, Ell6.I, WITH AFTERCOOLER, 12-5-2003]: PM: (9) [RULE 404, El93.lI, TURBOCHARGER, 2500 HPWITH 2-7-1986] K67.5 A/N: 451776 GENERATOR, 2000 KW



### • (1) (lA) (IB) Denotes RECLAIMemission factor (2) (2A) (28) Denotes RECLAIM emission rate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (5A) (58) Denotes command and control emission limit (6) Denotes airtoxic control rule limit (7) Denotes NSR applicability limit (8) (8A) (SB) Denotes 40 CFRlimit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (IO) See section J for NESHAPIMACT requirements ** Refer to sectionF and G ofthis permitto determine the monitoring, recordkeeping andreporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: .t..t. Facility ID: 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywiththe terms and conditions setforth below: Equipment ID 

### Connected RECLAIM Emissions• Conditions No. 

### To Source Type/ And Requirements Monitoring Unit

INTERNAL COMBUSTION ENGINE. Dl95 NOX: PROCESS CO: 0.67 GRAM/BHP-HR(4) B6LI. Cl.6. EMERGENCY POWER. LEAN BURN. UNIT** [RULE 1703

- PSD Analysis, Dl2.12, #I,TURBOCHARGED, DIESEL FUEL. 10-7-1988; 40CFR60 Subpart Dl2.13, CATERPILLARMODEL 3516C. 1111, 7-11-2006]; NOX: 3.7 Ell6.2, WITH A JOHNSON MATTHEY CRT GRAM/BHP-HR (4) [RULE 1703 El93.6, PARTICULATE FILTER WITH HIGH

- PSD Analysis, 10-7-1,88; E193.10, EFFICIENCY PARTICULATE AIR RULE2005, H-2005]; NOX: 469 E448.I. FILTER. TURBOCHARGER, 3622 HP LBS/1000 GAL DIESEL (I) E448.2. WITH [RULE 2012, 5-6-2005]; PMlO: E448.3, K67.7 A/N: 554366 0.007 GRAM/BHP-HR (4) [RULE 1303(a)(l}-BACT,S-10-1996; RULE/303(a)(J)-BACT, 12-6-2002];

### voe: 02s GRAM/BHP-HR (4) [RULE 1303(a)(l}-BACT,5-10-1996; RULE/303(a)(J)-BACT, 12-6-2002]
TANK. DIESEL STORAGE, 2,800 E202 GALLONS. SHAREDWITH D196



### • (I) (IA) (18) Denotes RECLAIM emission factor (2) (2A) (2B) Denotes RECLAIM emissionrate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (5A) (58) Denotes command and control emission limit (6) Denotes airtoxic control rule limit (7) Denotes NSR applicability limit (8) (SA) (88) Denotes40 CFR limit (e.g. NSPS. NESHAPS,etc.) (9) See App B for Emission Limits (IO) See sectionJ for NESHAP/MACTrequirements •• Refer to section Fand G ofthis permitto detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-41 78 Section D Page· 23 Facilitv ID· 800074 Revision#: 28 Date: January 14,2015 

## FACILITYPERMITTOOPERATE LACITY,DWP BAYNESGENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shall complywith theterms and conditions set forth below: Equipment ID Connected No. To

INTERNAL COMBUSTIONENGINE, EMERGENCY POWER, LEAN BURN, #2, TURBOCHARGED, DIESEL FUEL, CATERPILLAR, MODEL 3516C, WITH AJOHNSON MATTHEY CRT PARTICULATE FILTER, WITH HIGH EFFICIENCY PARTICULATEAIR FILTER: TURBOCHARGER: 3622 HP WITH A/N: 554367 Dl96

TANK, DIESEL STORAGE, 2,800 E203 GALLONS, SHARED WITH D195

STORAGETANK, NO. I, AQUEOUS AMMONIA, CARBON STEEL, 38233 GALS; DIAMETER: I4 FT; HEIGHT: 38FT 61N A/N: 272086 STORAGE TANK, NO. 2, AQUEOUS AMMONIA, CARBON STEEL, 38233 GALS; DIAMETER: I4 FT; HEIGHT: 38FT 6IN A/N: 272087 D34

D35



## • (1) (IA) (IB)Denotes RECLAIM emission factor C40 C4I

C40C41

(3) Denotes RECLAIM concentrationlimit (5) (5A) (SB) Denotes command and control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits 

### RECLAIM Source Type/ Monitoring Unit

NOX: PROCESS UNIT** Emissions* 

### And Requirements

CO: 0.67 GRAM/BHP-HR (4) (RULE 1703-PSDAnalysis, 10-7-1988; 40CFR60 Subpart IIII,7-11-2006]; NOX: 3.7 GRAM/BHP-HR (4) [RULE 1703

- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005];NOX: 469 LBS/1000 GAL (I) [RULE 2012, 5-6-2005]; PM: 0.007 GRAM/BHP-HR (4) [RULE 1303(a)(l)-BACT,5-10-1996; RULE/303(a)(1)-BACT, 12-6-20021;voe: 0.25 GRAM/BHP-HR (4) [RULE 1303(a)(l)-BACT,5-10-1996; RULE /303(a)(l)-BACT, 12-6-2002]

(2) (2A) (28) Denotes RECLAIM emission rate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit 

### Conditions

861.1, CI.6, Dl2.12, Dl2.13, Ell6.2, E193.6, El93.IO, E448.l, E448.2, E448.3, K67.7

CI57.I, EI44.I

CI57.I, El44.l

(8) (8A) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (I0) See section J for NESHAP/MACT requirements ** Refer to section F and G ofthis permit to determine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 24 Facilit)' ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operator shallcomply withthe terms and conditions setforth below: Equipment ID Connected No. 

### To

STORAGETANK. NO. 3, AQUEOUS AMMONIA, 3S233 GALS: DIAMETER: 14 FT: HEIGHT: 3S FT 6 IN AIN:2720SS STORAGETANK, NO. 4, AQUEOUS AMMONIA, 38233 GALS: DIAMETER: 14 FT: HEIGHT: 3S FT 6 IN AIN: 2720S9 STORAGE TANK, NO. 5, AQUEOUS AMMONIA, 3S233 GALS: DIAMETER: 14 FT: HEIGHT: 3S FT 6 IN AIN:272090 STORAGETANK, NO. 6, AQUEOUS AMMONIA, 3S233 GALS: DIAMETER: 14 FT: HEIGHT: 3S FT 6 IN AIN:272091 SCRUBBER, PACKEDBED, NO. I, VERTICAL PACKEDTYPE, POLYPROPYLENE PACKING, HEIGHT: 9 FT 3 IN: DIAMETER: SIN AIN: 272090 SCRUBBER, PACKED BED, NO. 2, VERTICAL PACKEDTYPE, POLYPROPYLENE PACKING, HEIGHT: 9 FT 3 IN: DIAMETER: S IN AIN:272090 STORAGETANK, UNIT NO. I, MAGNESIUM COMPOUNDS, FUEL OIL ADDITIVE, 350GALS AIN: 410730 D36

D37

03S

039

C40

C41

021



### • (I) (IA) (IB) Denotes RECLAIMemission factor C40C41

C40C41

C40C41

C40C41

034DJ5 036 DJ7DJS 039

D34 DJS D36 DJ7 DJS 039

(3) DenotesRECLAIMconcentrationlimit (5) (SA) (SB) Denotes commandandcontrol emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits 

### RECLAIM SourceType/

Monitoring Unit Emissions* 

### And Requirements

(2) (2A) (28) Denotes RECLAIMemissionrate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit 

### Conditions

Cl57.I, E144.l

Ci57.I. El44.l

El44.l

Cl57.I, El44.I

CS.I, Dl2.I, K67.2

Dl2.I, K67.2

(S) (8A) (SB) Denotes 40 CFR limit(e.g. NSPS, NESHAPS, etc.) (I0) See section J for NESHAP/MACT requirements •• Refer to sectionF and G ofthis pennitto determine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178 Section D Page: 25 Facilitv ID: 800074 Revision # 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LA CITY,DWPBAYNESGENERATING STATION SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFICCONDITIONS The operatorshall complywiththe terms and conditions set forth below: Equipment ID Connected RECLAIM Emissions

# . Conditions No. To SourceType/ And Requirements Monitoring Unit**'~ocel!ifSF** 

# ·**1N.aacAN.BcHJlicAt'lfoiQ~1f -~,**  

# "D'E'''''

, ______,-,- - '**-,~** - _,-_ - ,, -**~----~** STORAGETANK. UNIT NO. 2, D22 MAGNESIUM COMPOUNDS, FUEL OIL ADDITIVE, 350 GALS A!N:410732**;.P;roc~~;**

### P~~OL~~S~~~G~ 

### -:2;;;.. •••••• 

### . ..·-.· FfiV ,;;,r]!:":: 

## _,,g,,:• . :,_·,]::'

.. 

### . 

## ;[,,
STORAGE TANK, FIXED ROOF, D46 H23.I STEAM HEATED, NO. 172,003-A, FUEL OIL, 172000BBL; DIAMETERi 160 FT; HEIGHT! 48 FT A!N: C25861 STORAGE TANK, FIXED ROOF, D47 H23.I STEAM HEATED, NO. 172,001-B, FUEL OIL, 172000 BBL; DIAMETER: 160 FT; HEIGHT: 48 FT A/Ni C25859 STORAGE TANK, FIXED ROOF, D48 H23.I STEAM HEATED, NO. 172.002-C, FUEL OIL, 172000 BBL; DIAMETER! 160 FT; HEIGHT! 48 FT A/Ni C25860 STORAGE TANK, FIXED ROOF, D49 H23.I STEAM HEATED, NO. 200,001-D, FUEL OIL, 200000 BBL; DIAMETERi 160 FT; HEIGHT! 56 FT A/Ni C25862 STORAGE TANK, FIXED ROOF, D50 H23.I STEAM HEATED, NO. 300,001-E, FUEL OIL, 300000BBL; DIAMETER: 200 FT; HEIGHT: 56 FT A/Ni C25863 TANK, UNIT NO. I, TURBINE LUBE Dll C27 PM! (9) [RULE 404, 2-7-1986] OIL RESERVOIR A/Ni 122505 

## • (I) (IA) (IB)Denotes RECLAIMemission factor (2) (2A) (28) Denotes RECLAIM emission rate (3) Denotes RECLAIMconcentration limit (4) Denotes BACTemission limit (5) (SA) (58)Denotes command and control emission limit (6) Denotes air toxic control rule limit (7) Denotes NSR applicability limit (8) (SA) (88) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (10) See sectionJ for NESHAP/MACTrequirements •• Refer to section F and G ofthis permitto determine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 26 Facilitv ID: 800074 Revision#; 28 Date: January 14. 201 S 

## FACILITYPERMITTOOPERATE LACITY,DWPHAYNES GENERATING STATION SECTIOND: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operatorshall complywiththeterms and conditions set forth below: Equipment ID Connected RECLAIM Emissions• Conditions No. To Source Type/ And Requirements Monitoring Unit**~~ri'lces:~:q.**

## PE"6Li:9'STO~·.::;s:••· ···n;:;::?'>

## ···::q:(~r·::;:**~,.:~** TANK, UNIT NO. I,TURBINE DI2 C27 PM: (9) [RULE 404, 2-7-1986] GOVERNOR OIL RESERVOIR A/N: 12250S ELECTROSTATIC PRECIPITATOR, C27 Dll DI2 0323.1 NO. I, SMOG HOG, MODEL SH-I0-PE, TWO STAGE, PENNY TYPE, 60 KW A/N: 122S05 TANK, UNIT NO. 2, TURBINE LUBE 013 C28 PM: (9) [RULE 404, 2-7-1986] OIL RESERVOIR A/N: 122S06 TANK, UNIT NO. 2, TURBINE 014 C28 PM: (9) [RULE404,2-7-1986] GOVERNOR OIL RESERVOIR A/N: 122S06 ELECTROSTATIC PRECIPITATOR, C28 Dl3 D14 0323.I NO. 2, SMOG HOG, MODEL SH-10-PE, TWOSTAGE,PENNYTYPE, 60KW A/N: 122506 TANK, UNIT NO. 3.TURBINE LUBE DIS C29 PM: (9) [RULE 404,2-7-1986] OIL RESERVOIR A/N: 122S07 TANK, UNIT NO. 3,TURBINE D16 C29 PM: (9) [RULE 404, 2-7-1986] GOVERNOROIL RESERVOiR A/N: 122S07 ELECTROSTATIC PRECIPITATOR, C29 DIS DI6 0323.1 NO. 3, SMOG HOG, MODEL SH-10-PE, TWO STAGE, PENNEY TYPE, 60 KW A/N: 122S07 TANK, UNITNO. 4, TURBINE LUBE Dl7 C30 PM: (9) [RULE404, 2-7-1986] OIL RESERVOIR A/N: 122S08 TANK, UNIT NO. 4,TURBINE 018 C30 PM: (9) [RULE404,2-7-1986] GOVERNOR OIL RESERVOIR A/N: 122S08 

## • (I) (IA) (IB) Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIMemission rate (3) Denotes RECLAIM concentrationlimit (4) Denotes BACTemission limit (5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit (7) Denotes NSRapplicability limit (8) (SA) (8B) Denotes 40CFR limit (e.g. NSPS, NESHAPS,etc.) (9) See App B for Emission Limits (JO) See sectionJ forNESHAP/MACT requirements •• Refer to section Fand Gofthis permit to detennine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 27 Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY,DWP HAYNES GENERATINGSTATION SECTIOND: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFICCONDITIONS The operatorshall complywiththeterms and conditions set forth below: Equipment

ELECTROSTATIC PRECIPITA TOR. NO. 4.SMOG HOG, MODEL SH-10-PE, TWO STAGE, PENNEY TYPE, 60 KW NN·. 122508 TANK, UNIT NO. 5, TURBINE LUBE OIL RESERVOIR NN: 122509 ELECTROSTATIC PRECIPITATOR. NO. 5. SMOG HOG, MODEL SH-10-PE, TWO STAGE, PENNEYTYPE. 60 HP NN: 122509 TANK, UNIT NO. 6, TURBINE LUBE OIL RESERVOIR NN: 1225!0 ELECTROSTATIC PRECIPITA TOR. NO. 6. SMOG HOG. MODEL SH-10-PE, TWO STAGE, PENNEY TYPE, 60 KW NN: 1225!0

STORAGE TANK, FIXED ROOF, SETTLING TANK, LUBE OIL/WATER. VENTED TO ATMOSPHERE. 64()0 GALS; DIAMETER: 12 FT; HEIGHT; 8 FT WITH NN: 465115
HEATER. I KW ID Connected No. To

C30 Dl7 DI8

Dl9 C31

C31 DI9

DIOO C32

C32 OIOO

Dll6 RECLAIM SourceType/ Monitoring Unit Emissions* And Requirements

PM: (9) [RULE404, 2-7-1986]

PM: (9) [RULE 404, 2-7-1986]



### • (I) (IA) (IB) Denotes RECLAIMemission factor (2) (2A) (28) Denotes RECLAIM emission rate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (SA) (58) Denotes command and control emission limit (6) Denotes air toxic control rule limit Conditions

D323.I

D323.I

D323.I

H23.3

(7) DenotesNSR applicability limit (8) (SA) (88) Denotes 40CFR limit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (10) See section J for NESl-IAPIMACT requirements •• Refer to section F and Gofthis permit to determine the monitoring, recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 28 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LA CITY,DWPHA YNES GENERATING STATION SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS Theoperatorshall comply withtheterms and conditions set forth below: Equipment

STORAGETANK, FIXED ROOF, RETENTION, LUBE OIL/WATER, VENTED TOATMOSPHERE. 70 GALS; DIAMETER: 2 FT; HEIGHT: 3 FT SIN WITH A/N: 465115 HEATER, I KW STORAGETANK, FIXED ROOF. MECHANICAL SKIMMER. LUBE OIL/WATER. VENTED TO ATMOSPHERE, 595 GALS; DIAMETER: 4 FT 3.24 IN; HEIGHT: 5 FT 71N AIN: 465115 STORAGE TANK, FIXED ROOF, SKIM. LUBE OIL/WATER. VENTED TOATMOSPHERE. 90GALS; WIDTH: I FT 6 IN; HEIGHT: 5FT; LENGTH: 2FT A/N:465115 SUMP. WASTE WATER. VENTED TOATMOSPHERE. 3800 GALS; WIDTH: 6FT; HEIGHT: 9 FT 8.4 IN; LENGTH: 8 FT 7 IN WITH A/N:465115
PUMP, VENTEDTO ATMOSPHERE SUMP.WASTE OIL, VENTED TO ATMOSPHERE, 4700GALS; WIDTH: 5 FT 9.6 IN; HEIGHT: 9 FT 8.4 IN; LENGTH: II FT 6 IN A/N: 465115 ID Connected 

### No. To

Dll8

Dll9

Dl20

Dl22



## • (I) (IA) (IB) Denotes RECLAIM emission factor (3) Denotes RECLAIM concentration limit (5} (SA) (58) Denotes commandand control emission limit (7) Denotes NSR applicability limit (9) See App B for Emission Limits RECLAIM Source

### Type/ Monitoring Unit Emissions* And Requirements

(2) (2A) (2B) Denotes RECLAIMemissionrate (4) Denotes BACT emission limit (6) Denotes air toxic control rule limit Conditions

H23.3

H23.3

H23.3

H23.3

H23.3

(8) (SA) (8B) Denotes 40 CFRlimit (e.g. NSPS, NESHAPS, etc.) (10) See section J for NESHAP/MACT requirements •• Refer to section F and G ofthis permit to detennine the monitoring.recordkeeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Facilitv ID: Revision#: Page: 29 800074 28 Date: January 14,2015 

## FACILITYPERMITTOOPERATE LA CITY,DWPHAYNES GENERATING STATION SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFICCONDITIONS The operatorshall complywith the terms and conditions set forth below: Equipment ID Connected RECLAIM Emissions

### • Conditions No. To Source Type/ And Requiremeots Monitoring Unit

### !c~roc~~**·(jjl!WA1'1:SEt5-tlQI~''•'~** :EE : .· ····'''

..·. 

## '·T·<:':·:.:· •**~ ~·.:"._.,,,,.,,,**  STORAGE TANK, WASTE WATER. Dl23 H23.3 VENTED TO ATMOSPHERE, 6400 GALS: DIAMETER: 12 FT; HEIGHT: 8 FT WITH AIN: 465115
HEATER. I KW SUMP.CONTAMINATEDWATER. Dl54 H23.3 COVERED, 3200 GALS; 2 TOTAL A/N: 465115 TANK, BOILER FRONT WASTE, 250 0155 H23.3 GALS AIN: 465115 WASTE WATER SEPARATOR. #I, Dl98 MAKE: HIGHLAND, MODEL: HTJ2000. 12000 GALS/HR; 2000 GALS A/N: 495673 WASTE WATER SEPARATOR, #2, Dl99 MAKE: HIGHLAND, MODEL: HTJ2000, 12000 GALS/HR; 2000 GALS A/N: 495674 WASTE WATER SEPARATOR, #3, 0200 MAKE: HIGHLAND, MODEL: HTJ2000, 12000 GALS/HR: 2000 GALS AIN: 495675



### • (I) (IA) (IB)Denotes RECLAIM emission factor (2) (2A) (28) Denotes RECLAIM emission rate (3) Denotes RECLAIM concentration limit (4) Denotes BACT emission limit (5) (5A) (5B) Denotes command and control emission limit (6) Denotes air toxic control rule limit (7) Denotes NSR applicability limit (8) (&A) (88) Denotes 40CFRlimit (e.g. NSPS, NESHAPS, etc.) (9) See App B for Emission Limits (10) See section J for NESHAP/MACT requirements •• Refer to section F and G ofthis permit to determine the monitoring, recordk.eeping and reporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 30 Facility ID: 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LA CITY,DWPHAYNES GENERATING STATION SECTION D: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS The operatorshallcomplywith theterms and conditions set forth below: Equipment

WASTE WATER SEPARATOR, MAKE: PSI, MODEL: PSC-I000, UNDERGROUND, 6000GALS/HR: !000 GALS: DIAMETER: 4FT: LENGTil: I5 FT 8 IN A/N: 53098I
ABRASIVE BLASTING, OPEN, KELCO, MODEL I24, 600 LBS CAPACITY, TWO NOZZLES, DIAMETER: .3I IN A/N: I23I7I ID Connected 

### No. To

D20I

D56

SUMP, RAINWATER, 069 UNDERGROUND, 420 BBL: WIDTH: I7FT 6 IN: DEPTH: 7FT 9 IN: LENGTil: I7FT 6 IN

RULE 2I9 EXEMPT EQUIPMENT, ABRASIVE BLASTING EQUIPMENT, GLOVE-BOX,<= 53 FTJ, WITH DUST FILTER RULE 2 I 9EXEMPT EQUIPMENT, AIR COND!TlONING UNITS RULE 2I9 EXEMPT EQUIPMENT, REFRIGERATION UNITS RULE 2I9 EXEMPT EQUIPMENT, COATING EQUIPMENT, PORTABLE, ARCHITECTURAL COATINGS E112

Ell3
EII4
EI24



### • (1) (IA) (IB)Denotes RECLAIM emission factor (3) Denotes RECLAIMconcentration limit (5) (SA) (58)Denotes command andcontrol emissionlimit (7) Denotes NSRapplicability limit (9) See App B for Emission Limits RECLAIM Source Type/ Monitoring Unit Emissions• And Requirements

PM: (9) [RULE 1140. 2-1-1980; RULE 1140, 8-2-1985; RULE 405. 2-7-I986]

PM: (9) [RULE 1146. 2-I-1980; RULE 1140, 8-2-1985; RULE404, 2-7-I986; RULE 405. 2-7-1986] Conditions

D323.2

0322.I, D38l.l, K67.I

H23.5
H23.6
ROG: (9) [RULE 1113, 11-8-I996; K67.3 RULE 1113, 7-13-2007; RULE 1171, 11-7-2003; RULE 1171, 2-1-2008]
(2) (2A) (2B) Denotes RECLAIM emission rate (4) Denotes BACT emission limit (6) Denotes airtoxic control rule limit (8) (8A) (8B) Denotes 40 CFR limit (e.g. NSPS, NESHAPS, etc.) (10) See section J forNESHAP/MACT requirements •• Refer to sectionF and G ofthis permitto determine the monitoring, recordkeeping andreporting requirements for this device.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-41 78



## FACILITYPERMITTOOPERATE Section D Page: 31 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION
SECTIOND: DEVICE IDINDEX

Thefollowing sub-section provides an index tothe devices thatmake u_p thefacility description sorted bydevice ID.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 32 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHA YNES GENERATING STATION SECTIOND: DEVICE IDINDEX

DI I I I 04 2 

### I I Oil 25 6 0 012 26 6 0 013 26 6 0 014 26 6 0 015 26 6 0 016 26 6 0 017 26 6 0 018 26 6 0 019 27 6 0 021 24 5 0 022 25 5 0 C27 26 6 0 C28 26 6 0 C29 26 6 0 C30 27 6 0 C31 27 6 0 C32 27 6 0 034 23 5 0 035 23 5 0 036 24 5 0 037 24 5 0 038 24 5 0 039 24 5 0 C40 24 5 0 C41 24 5 0 046 25 6 0 047 25 6 0 048 25 6 0 049 25 6 0 050 25 6 0 053 21 4 0 056 30 8 0 069 30 9 0,; 

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 33 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY, DWPHAYNES GENERATING STATION SECTIOND: DEVICE ID INDEX
Device IndexForSection D

### D!l:~~' 

### ID ;ii: 

### S • DP ':No. ·

# .....**~~**

### .,;£f~~tell\,,~,; 

## ;;.. ;<**~** .**~·** •.... ;;;jj;;;; _:__-i[>_i;,.,I;•. ' -. ,' ,-r"'

..... .

,_,,)hB£i>U·+ ·"'**''>~'°""·''::.** ''""' ,. C73 I I I C74 I I I C75 2 I I C76 2 I I S96 2 I I S97 3 I I 0100 27 6 0 E112 30 10 0 El 13 30 10 0 El 14 30 10 0 DI 16 27 7 0 0117 28 7 0 0118 28 7 0 0119 28 7 0 0120 28 7 0 0122 28 7 0 0123 29 7 0 El24 30 10 0 0125 5 2 0 0129 5 2 0 Cl30 6 2 0 CBI 6 2 0 Sl33 6 2 0 0134 8 2 0 Cl38 9 2 0 Cl39 9 2 0 Sl41 9 2 0 0142 8 2 0 0154 29 7 0 0155 29 7 0 0159 10 3 0 Cl61 11 3 0 Cl62 11 3 0 Sl64 11 3 0 0165 12 3 0

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 34 Facility ID: 800074 Revision#: 28 Date: January 14. 2015



## LACITY,DWPHAYNES GENERATINGSTATION SECTIOND: DEVICE ID INDEX
Device IndexForSection D

## 3,,p~~· g

## fi1~~~~-1R.r~,~~.:-._,;:,1-;~~:1i !.

# ~··~ Cl67 13 3 0 Cl68 13 3 0 Sl70 13 3 0 0171 14 3 0 Cl73 15 3 0 Cl74 15 3 0 Sl76 15 3 0 0177 16 3 0 Cl79 17 3 0 Cl80 17 3 0 Sl82 17 3 0 0183 18 3 0 C185 19 3 0 C186 19 3 0 Sl88 19 3 0 0189 20 3 0 Cl91 21 3 0 Cl92 21 3 0 Sl94 21 3 0 0195 22 4 0 0196 23 4 0 0198 29 7 0 0199 29 7 0 0200 29 7 0 0201 30 7 0 E202 22 4 0 E203 23 4 0

### South Coast Air Quality Management District Z1865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 35 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWP HAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywiththe terms and conditions setforth below:
FACILITY CONDITIONS
F9.I Except for open abrasive blasting operations, the operator shall not discharge into the atmosphere from any single source of emissions whatsoever any air contaminant for a period orperiods aggregating more than three minutes in any one hourwhich is: (a) As dark or darker in shade as that designated No.I on the Ringelmann Chart, as published by the United States Bureau ofMines; or (b) Of such opacity as to obscure an observer's view to a degree equal to or greater than does smoke described in subparagraph (a) ofthis condition. [RULE 401, 3-2-1984; RULE 40I, 11-9-200I) Fl4.I The operator shall not use fuel oil containing sulfur compounds in excess of 0.05 percent by weight. The .05 percent sulfur limit shall not apply to existing supplies of any liquid fuel in storage as ofOctober I, 1993 until such supply is exhausted. [RULE 431.2, 5-4-1990; RULE 431.2, 9-15-2000) Fl4.2 The operator shall not purchase fuel oil containing sulfur compounds m excess of 15 ppm by weight as supplied by the supplier. This condition shall become effective on orafter June I, 2004.
[RULE 431.2, 9-15-2000) Fl6.I The operator shall keep records, in a manner approved by the District, for the following parameter(s) or item(s):

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 36 Facilitv ID: 800074 Revision #: 28 Date: January 14. 2015



## LACITY,DWPHA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith theterms and conditions set forth below: purchaserecords offuel oil and sulfur content ofthe fuel
[RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] F18.l Acid Rain S02Allowance Allocation for affected units are as follows:
Device ID Boiler ID Contaminant Tons in any year I 4 71 5 7 9 BoilerNo. I S02 571 BoilerNo. 2 S02 328 BoilerNo. 3 S02 1131 BoilerNo. 4 S02 851 Boiler No. 5 S02 1205 BoilerNo. 

### 6 S02 1270 a). The allowance allocation(s) shall apply to calendaryears 2010 and beyond. b). The number of allowances allocated to Phase II affected units by U.S. EPA may change in a 1998 revision to 40CFR73 Tables 2,3, and 4. In addition, the number of allowances actually held by an affected source in a unit account may differ from the number allocated by U.S. EPA. Neither of the aforementioned conditions necessitate a rev1s1on to the unit S02 allowance allocations identified in this permit (see 40 CFR 72.84) [40CFR73 SubpartB, 1-11-1993]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Section D Page: 37 Facility ID: 800074 Revision#· 28 Date: January 14. 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS

Theoperator shall comply with the terms and conditions setforth below:

F24.I Accidental release prevention requirements ofSection I12(r)(7): a). The operator shall comply with the accidental release prevention requirements pursuant to 40 CFR Part 68 and shall submit to the Executive Officer, as a part of an annual compliance certification, a statement that certifies compliance with all of the requirements of 40 CFR Part 68, including the registration and submission of a risk management plan (RMP). b). The operator shall submit any additional relevant information requested by the Executive Officeror designated agency. [ 40CFR68

- Accidental Release Prevention, 5-24-1996] 

### DEVICE CONDITIONS
A. Emission Limits A63.2 The operator shall limit emissions from this equipment as follows:
CONTAMINANT 

## co PMIO 

## voe SOX EMISSIONS LIMIT Less than or equal to 18842 LBS IN ANY ONE MONTH Less than or equal to I0784 LBS IN ANY ONE MONTH Less than or equal to 4409 LBS IN ANY ONE MONTH Less than or equal to 327 LBS IN ANY ONE MONTH

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178



## FACILITYPERMITTO OPERATE Section D Page: 38 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomply with theterms and conditions set forth below: The operator shall calculate the emission limit(s) by using calendar monthly fuel use data and the following emission factors: Natural Gas: PMI0

### = 7.50 

### lbs/MMscf, VOC 

### = 2.58 lbs/MMscf, and SOx 

### = 0.21 lbs/MMscf. Diesel Fuel: PMIO 

### = 1.67 lbs/Mgal, VOC 

### =0.52 lbs/Mgal, and SOx

### =0.21 lbs/Mgal. The operator shall calculate the emission limit(s) , after the CO CEMS certification, based on the readings from the certified CO CEMS. In the event the CO CEMS is not operating, has been certification tested but is not certified, or the emissions exceed the valid upper range of the analyzer, the emissions shall be calculated in accordance with the approved CEMS plan. During diesel readiness testing, the CO shall be calculated using the fuel use data and a 24.2 lbs/Mgal emission factor The operator shall calculate the emission limit(s) for CO in the absence of valid CEMS data, by using the monthly fuel use data and the following factor: Natural Gas: 9.03 lbs/MMscf For the purposes of this condition, the limit(s) shall be based on the total combined emissions from combined cycle gas turbine No. I0 and it's associated duct burner during any calendar month. The duct burner shall not be operated when the turbine is firing diesel fuel. (RULE 1303(b)(2)-0ffset,5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] [Devices subjectto this condition: DJ34, Dl42] A63.3 The operator shall limit emissions from this equipment as follows:
CONTAMINANT 

## co PMIO 

## voe SOX EMISSIONS LIMIT Less than orequal to 18842 LBS IN ANY ONE MONTH Less than orequal to I

### 0784 LBS IN ANY ONE MONTH Less than or equal to 4409 LBS IN ANY ONE MONTH Less than or equal to 327 LBS IN ANY ONE MONTH

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 39 Facilitv ID: 800074 Revision#: 28 Date: January 14, 201 S



## LA CITY,DWP HAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall comply with theterms andconditions set forth below:
The operator shall calculate the emission limit(s) by using calendar monthly fuel use data and the following emission factors: Natural Gas: PMIO = 7.50 lbs/MMscf, VOC 

### = 2.58 lbs/MMscf, and SOx 

### = 0.21 lbs/MMscf. Diesel Fuel: PMIO

### = 1.67 lbs/Mgal, VOC = 0.52 lbs/Mgal, and SOx = 0.21 lbs/Mgal. The operator shall calculate the emission limit(s) , after the CO CEMS certification, based on the readings from the certi ed CO CEMS. In the event the CO CEMS is not operating, has been certification tested but is not certified, or the emissions exceed the valid upper range of the analyzer, the emissions shall be calculated in accordance with the approved CEMS plan. During diesel readiness testing, the CO shall be calculated using the fuel use data and a 24.2 lbs/Mgal emission factor For the purposes of this condition, the limit(s) shall be based on the total combined emissions from combined cycle gas turbine No. 9 and it' s associated duct burner during any calendar month. The duct burner shall not be operated when the turbine is firing diesel fuel. [RULE 1303(b)(2)-0ffset,5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] [Devices subject to this condition: D125, D129] A63.4 The operator shall limit emissions from this equipment as follows:
CONTAMINANT 

## co PMIO 

## voe SOX EMISSIONS LIMIT Less than or equal to 11755 LBS IN ANY ONE MONTH Less than orequal to 3341 LBS IN ANY ONE MONTH Less than orequal to 2272 LBS IN ANY ONE MONTH Less than or equal to 90 LBS IN ANY ONE MONTH

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 40 Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall complywith the terms and conditions set forth below: The above limits apply to each turbine. The operator shall calculate the emission limit(s) by using calendar monthly fuel use data and the following em1ss10n factors: VOC: 4.42 lbs/mmscf, PMIO: 6.5 lbs/mmscf, SOx: 0.18 lbs/mmscf. The operator shall calculate the em1ss10n limits for CO after the CO CEMS certification based upon readings from the AQMD certified CEMS. In the event the CO CEMS is not operating or the emissions exceed the valid upper range of the analyzer, the emissions shall be calculated by using monthly fuel use data and the following factor: CO: 22.88 lbs/mmscf. [RULE 1303(b)(2)-0ffset,S-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] [Devices subject to this condition: Dl59, Dl65, DI71, DI77, Dl83, DI 89] A99.l The I0 PPM NH3 emission limit(s) shall not apply when ammonia injection has not commenced. (NH3 emissions). [RULE 1303(a)(l)-BACT, S-10-1996; RULE l303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition :C73, C75] A99.2 The 2 PPM NOX emission limit(s) shall not apply during turbine startups, diesel readiness testing, or shutdowns. Shutdowns shall not exceed 30 minutes/event. Written records of startups and shutdowns shall be maintained and made available to the AQMD upon request.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 41 Facility ID: 800074 Revision #: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall comply with theterms and conditions setforth below: For the purposes of this condition, cold start up shall be defined as a start up which occurs after the steam turbine has been shutdown for 72 hours or more. A non-cold start up shall be defined as a start up which occurs after the steam turbine has been shutdown for less than 72 hours. The beginning of start up occurs at initial fire in the combustor and the end of start up occurs when the BACT levels are achieved. No more than one turbine shall be in cold start-up mode at any one time. The turbines shall not be started on diesel fuel. For the purposes of this condition, steam turbine shutdown period shall be defined as the number of hours between the closing and reopening of the steam stop valve. The operator shall keep records of the date and time of the steam stop valve opening and closing, and make these records available to AQMO personnel upon request. [RULE 2005, 5-6-2005] [Devices subject to this condition: Dl25, 0129, 0134, D142] A99.3 The 4 PPM CO emission limit(s) shall not apply during turbine startups, diesel readiness testing, or shutdowns. Shutdowns shall not exceed 30minutes/event. Written records of startups and shutdowns shall be maintained and made available tothe AQMO upon request. For the purposes of this condition, cold start up shall be defined as a start up which occurs after the steam turbine has been shutdown for 72 hours or more. A non-cold start up shall be defined as a start up which occurs after the steam turbine has been shutdown for less than 72 hours. The beginning of start up occurs at initial fire in the combustor and the end of start up occurs when the BACT levels are achieved. No more than one turbine shall be in cold start-up mode at any one time. The turbines shall not be started on diesel fuel. For the purposes of this condition, steam turbine shutdown period shall be defined as the number of hours between the closing and reopening of the steam stop valve. The operator shall keep records of the date and time of the steam stop valve opening and closing, and make these records available to AQMO personnel upon request.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 42 Facility ID: 800074 Revision#: 28 Date: January 14,2015



## LACITY,DWPHA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywiththeterms and conditions set forth below: [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002) [Devices subjectto this condition: D125, D129, D134, D142) A99.6 The 5.8 Lbs/hr PMIO emission limit(s) shall not apply during startup and shutdown periods

.. [RULE 1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002) [Devices subject to this condition: Dl59, D165, Dl71, DI77, D183, D189) A195.l The 2 PPMV NOX emission limit(s) is averaged over 60 minutes at 15 percent oxygen, dry. [RULE 2005, 5-6-2005) [Devices subject to this condition: D125, D129, Dl34, Dl42) Al95.2 The 4 PPMV CO emission limit(s) is averaged over 60 minutes, at 15 percent oxygen, dry.
[RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002) [Devices subject to this condition: D125, D129, D134, D142) Al95.3 The 2 PPMV VOC emission limit(s) is averaged over 60 minutes, at 15 percent oxygen, dry. The limit does not apply during diesel readiness tests. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition: Dl25,D129, Dl34, Dl42)

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 43 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY, DWP HA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomply with theterms and conditions set forth below:

Al95.4 The 5 PPMV NH3 emission limit(s) is averaged over 60 minutes at 15 percent 02 dry. The operator shall calculate and continuously record the NH3 slip concentration using the following: NH3(ppmv)=[a-b*c/1E6]*1E6/b, where a=NH3 injection rate (lb/hr)/17 (lb/lb/mole), b=dry exhaust gas flow rate (lb/hr)/29(lb/lb/mole), and c=change in measured NOx across the SCR (ppmvd at 15 percent 02). The operator shall install and maintain a NOx analyzer to measure the SCR inlet NOx ppm accurate to within +/- 5 percent calibrated at least once every 12 months. The operator shall use the method described above or another alternative method approved by the Executive Officer. The ammonia slip calculation procedures described above shall not be used for compliance determination or emission information determination without corroborative data using an approved reference method for the determination of ammonia. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subjecttothis condition: Cl3l, Cl39] A195.5 The 5 PPMV NOX emission limit(s) is averaged over 720 operating hours (heat input weighted average).

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 44 Facility ID· 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywith theterms and conditions setforth below: A data acquisition system shall be installed and maintained to continuously calculate and record the NOx ppm based on the 720 operating hour average. The average shall be calculated based on emissions during all boiler operating hours except during: I. startups defined as whenever the unit is being brought up to normal operating temperature from an inactive status and the exhaust temperature entering the SCR catalyst is less than 530 degrees F; 2. shutdowns defined as whenever the unit is allowed to cool from a normal operating temperature to inactive status and the exhaust temperature entering the SCR catalyst is less than 530 degrees F; 3. calibration and maintenance periods, Part 75 linearity testing, RATA testing, equipmentbreakdown periods as defined in Rule 2004, and periods ofzero fuel flow.

The heat input weighted average NOx concentration shall be calculated using the following equation, orother equivalent equation. PPMV(3%02) = (Et/Qt)*K; where PPMV(3%02) = the concentration of NOx in PPMV at 3%02; K 

## = a conversion factor from lbs/MMBtu to PPM, which can be determined using EPA 40 CFR60 Method 19. The default K value is 819; Et 

## = Total reported NOx emissions during the averaging period including emissions reported as a result of missing data procedures pursuant to Rule 2012; Qt = Total heat input during the averaging period. [RULE 2009, 5-11-2001] [Devices subject to this condition : D1, 04] Al95.8 The 2.5 PPMV NOX emission limit(s) is averaged over 1hour, dry basis at 15 percent oxygen. This limit shall not apply during startup and shutdown periods.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 45 Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015



## LA CITY, DWPHAYNES GENERATING STATION

SECTION D: FACILITYDESCRIPTION ANDEQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith theterms and conditions setforth below: [RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] [Devices subject to this condition: Dl59, Dl65, Dl71, DI77, Dl83, Dl89] Al95.9 The 4 PPMV CO emission limit(s) is averaged over I hour, dry basis at 15 percent oxygen. This limit shall not apply during startup and shutdown periods. [RULE 1703

- PSD Analysis, 10-7-1988] [Devices subject to this condition: Dl59,Dl65,DI71, DI77, Dl83, Dl89] Al95.10 The 2 PPMV VOC emission limit(s) is averaged over I hour, dry basis at 15 percent oxygen. This limit shall not apply during startup and shutdown periods. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition : D159, Dl65, D171, DI77, DI83, DI89] A327.l For the purpose of determining compliance with District Rule 475, combustion contaminant emissions may exceed the concentration limit or the mass emission limit listed, but notboth limits at the same time. [RULE 475, 10-8-1976; RULE 475, 8-7-1978] [Devices subject to this condition Dl77,Dl83, Dl89] Dl25, Dl29, Dl34, Dl42, Dl59, Dl65, Dl71,
A433.l The operator shall comply at all times with the 2.0 ppm I hour BACT limit for NOx, except as specified in Conditions A99.2, and for the following operating scenarios:: Operating 

# IMaximum Hourly Emission 

# IOperational Limit Scenario Limit

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Page: 46 Facilitv ID: 800074 Revision#: 28 Date: January 14,2015 

## FACILITYPERMITTOOPERATE LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall complywith theterms and conditions set forth below: Cold Start 

# I225 lbs/hr

Non-Cold Start 

# I 170 lbs/hr

[RULE 2005, 5-6-2005] 

# INOx emissions not to exceed 600 lbs total percold start. Cold startnotto exceed 360 minutes total, 4 starts permonth, and 48 starts peryear perturbine 

# INOx emissions notto exceed

300 lbs total pernon cold start. Non cold start notto exceed I80 minutes total, 27 starts per month, and 324 starts peryear per turbine

[Devices subject to this condition: Dl25, Dl29, Dl34,Dl42] 

### B. Material/FuelTypeLimits B59.l The operator shall only use the following material(s) in this device:
Air preheater elements that are made of corrosion resistant stainless steel, type 409 or equivalent A gunite lining in the flue gas duct surfaces between the air preheaters and exhaust stack, exceptfor the turning vanes, expansion joints, and related parts [RULE 401, 3-2-1984; RULE 401, 11-9-2001] [Devices subject to this condition : DI, D4]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 47 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION ANDEQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywiththeterms and conditions set forth below:

B59.3 The operator shall only use the following material(s) in this device : Diesel whichmeets the specifications ofRule 431.2
[RULE 431.2, 5-4-1990; RULE 431.2, 9-15-2000] [Devices subjecttothis condition :D53] B61.l The operator shall only use fuel oil containingthe following specified compounds: Compound total sulfur compounds calculated as H2S is less than ppm by weight 15

[RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 6-3-2011; RULE 431.2, 5-4-1990; RULE 431.2, 9-15-2000] [Devices subject to this condition: 0195, Dl96] B75.l The operator shall not use fuel oil in this equipment except under the following circumstance(s):

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page· 48 Facility ID: 800074 Revision#: 28 Date: January 14. 2015



## LA CITY,DWPHA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

The operatorshall comply with the terms and conditions set forth below: Interruption in natural gas service due to unforeseeable failure, malfunction, or natural disaster, not resulting from an intentional or negligent act or omission on the part ofthe owner or operator For diesel fuel readiness testing not to exceed 60 minutes per turbine per month. Fuel oil shall be low nitrogen, low sulfur diesel. Sulfur content shall not exceed 15 ppm by weight, or other more stringent limit specified in Rule 431.2. The operator shall keep records of the date diesel was used, the amount of diesel used, and the reason for use. These records shall be kept for a minimum of 5years and be made available for AQMD inspection upon request. Vendor specification for the initial and each subsequent shipment of diesel shall be maintained to verify sulfur and nitrogen content. If the vendor information is not available, the operator shall have a sample of each shipment of fuel analyzed by an independent lab for sulfur and nitrogen concentration. These records shall be kept for a minimum of5years and be made available for AQMD inspection upon request. For the above circumstances, diesel fuel shall not be used in this equipment unless water injection is fully employed. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 4-9-1999; RULE 2005,4-20-2001] [Devices subject to this condition: Dl25, Dl29, Dl34, D142] 

### C. Throughput orOperating ParameterLimits C1.3 The operator shall limit the operating time to no more than 199 hour(s) in any one year.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar. CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page· 49 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATINGSTATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywiththeterms and conditions set forth below: The 199 hours per year shall include no more than 50 hours m any one year for maintenance and testing purposes. The operation of the engine beyond the 50 hr/yr allotted for engine maintenance and testing shall be allowed only in the event of a loss of grid power or up to 30 minutes prior to a rotating outage, provided that the grid operator or electric utility has ordered rotating outages in the control area where the engine is located or has indicated that it expects to issue such an order at a certain time, and the engine is located in a utility service block that is subjectto the rotating outage
.. Engine operation shall be terminated immediately after the utility distribution company advises that a rotating outage is no longer imminent or in effect.. [RULE 1110.2, 2-1-2008; RULE 1470, 6-1-2007; RULE 2012, 5-6-2005] [Devices subject to this condition : D53] Cl.4 The operator shall limit the number ofstart-ups to no more than 150 in any one month. Startuptime shall not exceed 25 minutes per startup. NOxemission shall not exceed 20 lbs per startup. For the purpose of this condition, a startup shall be defined as the start up process to bring the turbine in full successful operation that complies with the BACT emission limits. Ifduring startup the process is aborted the process will count as one startup
.. The operator shall determine NOx emissions in lbs for each startup based on CEMS data. The startup NOx emissions shall be recorded in the CEMS. The operator shall maintain records in a manner approved by the District, for a minimum offive year, to demonstrate compliance with this condition.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178



## FACILITYPERMITTOOPERATE Section D Page: SO Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015



## LA CITY, DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

Theoperator shall complywiththeterms and conditions set forth below: [RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] [Devices subjectto this condition: Dl59, Dl65, Dl71, DI77, Dl83, Dl89] C1.5 The operator shall limit the number ofshut-downs to no more than 150 in any one month.
Shutdowntime shall not exceed I0 minutes per shutdown. For the purposes of this condition, a shutdown event shall be defined as the period beginning with the initiation of the combustion turbine shutdown sequence and ending with the cessation offiring ofthe combustion' turbine engine. The operator shall maintain records in a manner approved by the District, for a minimum offive years, to demonstrate compliance with this condition. [RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] [Devices subjecttothis condition: Dl59, Dl65, Dl71, DI77, Dl83,Dl89] C1.6 The operator shall limit the operating time to no more than 200 hour(s) in any one year.

### South Coast Air Quality Management District 21865 Copley Drive. Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 51 Facilitv ID: 800074 Revision#: 28 Date: Janwuy 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshallcomplywith theterms and conditions setforth below: The operation includes no more than 50 hours per year and 4.2 hours per month for maintenance and testing as required in rule 1470(c)(2). The operation includes 10 hours allowed for initial comrniss1onmg testing. The I0 hours commissioning operation shall not be included as part of the 50 hours per year operation for maintenance and testing. The operation of the engine beyond the50 hoursper year allotted for engme maintenance and testing shall be allowed only in the event of a loss of grid power or up to30 minutesprior to a rotating outage, provided that the electrical grid operator or electric utility has ordered rotating outages in the control area where the engine is located or has indicated that it expects to issue such an order at a certain time, and the engine is located in a utility service block that is subject to the rotating outage. Engine operation shall be terminated immediately after the utility distribution company advises that a rotating outage is no longer imminent orin effect. [RULE 1303(b)(l)-Modeling,5-10-1996; RULE 1303(b)(l)-Modeling, 12-6-2002; RULE 1303(b)(2)-0ffset,5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002; RULE 1470, 5-4-2012; 40CFR60 Subpartfill,7-11-2006] [Devices subject to this condition : D195, D196] CS.I The operator shall use this equipment in such a manner that the flow rate being monitored, as indicated below, is not less than 2.5 gpm. To comply with this condition, the operator shall monitor the flow rate as specified in condition number 12-1. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a){l)-BACT, 12-6-2002] [Devices subject to this condition :C40] C157.I The operator shall install and maintain a pressure reliefvalve set at 15 psig.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TOOPERATE Section D Page: 52 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

The operator shall comply with the terms and conditions set forth below:
[RULE 402, 5-7-1976] [Devices subject to this condition: D34, D35, D36, D37, D39] C177.I The operator shall set and maintain the fuel injection timing of the engme at 4 degrees retarded relative to standard timing. [RULE 2009, 5-11-2001] [Devices subjectto this condition :D53] 

### D. Monitoringffesting Requirements Dl2.I The operator shall install and maintain a(n) flow meter to accurately indicate the flow rate ofthe incoming scrubbing (city) water. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(1)-BACT, 12-6-2002] [Devices subjectto this condition: C40, C41] Dl2.2 The operator shall install and maintain a(n) temperature gauge to accurately indicate the temperature at the inlet ofeach selective catalytic reduction reactor. [RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 5-11-2001; RULE 2012, 12-5-2003] [Devices subject to this condition :C73, C75] D12.3 The operator shall install and maintain a(n) continuous monitoring system to accurately indicate the ammonia injection rate ofthe ammonia injection system.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 53 Facility ID: 800074 Revision#: 28 Date: January 14,2015



## LA CITY, DWP HAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshallcomply with theterms and conditions setforth below:
The operator shall also install and maintain a device to continuously record the parameter being measured. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition :C73, C75] D12.5 The operator shall install and maintain a(n) non-resettable elapsed time meter to accurately indicate the elapsed operating time ofthe engine. [RULE 1110.2, 2-1-2008; RULE 2012, 5-6-2005] [Devices subjectto this condition :D53] D12.6 The operator shall install and maintain a(n) temperature gauge to accurately indicate the temperature inthe exhaust at the inlet to the SCRreactor. The operator shall also install and maintain a device to continuously record the parameter being measured. The measuring device or gauge shall be accurate to within plus or minus 5percent. It shall be calibrated once every 12 months. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 5-11-2001; RULE 2012, 12-5-2003] [Devices subjectto this condition : C131, C139] 012.7 The operator shall install and maintain a(n) pressure gauge to accurately indicate the differential pressure across the SCR catalystbed in inches ofwater column.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 54 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith theterms and conditions set forth below: The operator shall also install and maintain a device to continuously record the parameterbeing measured. The measuring device or gauge shall be accurate to within plus or mmus 

### 5 percent. It shall be calibrated once every 12 months. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 5-11-2001; RULE 2012, 12-5-2003] [Devices subject to this condition : C131, C139] 012.8 The operator shall install and maintain a(n) continuous monitoring system to accurately indicate the ammonia injection rate ofthe ammonia injection system. The operator shall also install and maintain a device to continuously record the parameterbeing measured. The measuring device or gauge shall be accurate to within plus or minus 5 percent. It shall be calibrated once every 12 months. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition : C131, C139] D12.9 The operator shall install and maintain a(n) flow meter to accurately indicate the flow rate ofthe total hourly throughput ofinjected ammonia (NH3). The operator shall also install and maintain a device to continuously record the parameterbeing measured. The measuring device or gauge shall be accurate to within plus or minus 5percent. The accuracy ofthe device shall be verified once every 12 months. The ammonia injection rate shall remain between 74.9 and 143.9 lbs perhour.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 55 Facility ID: 800074 Revision#: 28 Date: January 14,2015



## LA CITY, DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION ANDEQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith theterms and conditions setforth below: [RULE 1703

- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] [Devices subjecttothis condition : C162, Cl68, Cl74, C180, C 186, Cl92] Dl2.IO The operator shall install and maintain a(n) temperature gauge to accurately indicate the temperature atthe inlet to the SCRreactor. The operator shall also install and maintain a device to continuously record the parameter being measured. The measuring device or gauge shall be accurate to within plus or minus 5percent. The accuracy ofthe device shall be verified once every 12 months. Ammonia injection shall be used at all times at an injection rate which minimizes NOX emissions whenever the exhaust temperature prior to the inlet of the SCR catalyst is between 734 F and 850 F as measured bythe temperature gauge. [RULE 1703- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] [Devices subject to this condition: Cl62, Cl68,Cl74, Cl80, Cl86,Cl92] Dl2.II The operator shall install and maintain a(n) pressure gauge to accurately indicate the differential pressure across the SCR catalystbed in inches water column. The operator shall also install and maintain a device to continuously record the parameter being measured. The measuring device or gauge shall be accurate to within plus or minus 5percent. The accuracy ofthe device shall be verified once every 12 months. The pressure differential shall be between 4.0 and 5.8 inches water column. [RULE 1703

- PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 56 Facilitv ID· 800074 Revision#· 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywith the terms and conditions set forth below:
[Devices subjectto this condition: Cl62, Cl68, Cl74, Cl80, Cl86, Cl92] Dl2.12 The operator shall install and maintain a(n) non-resettable elapsed time meter to accurately indicate the elapsed operatingtime ofthe engine. [RULE 1304(c)-OffsetExemption,6-14-1996; RULE 1470, 6-1-2007; 40CFR60 Subpart 1111, 7-11-2006] [Devices subjecttothis condition: Dl95, Dl96] Dl2.13 The operator shall install and maintain a(n) non-resettable totalizing fuel flow meter to accurately indicate the fuel usage ofthe engine. [RULE 2012, 5-6-2005] [Devices subjectto this condition : D195, D196] D28.3 The operator shall specifications: conduct source test(s) in accordance with the following

### South Coast Air Quality Management District 21865 Copley Drive. Diamond Bar, CA 91765-4178 Section D Facilitv ID· Revision#: Page: 57 800074 28 Date: January 14, 2015 

## FACILITYPERMITTO OPERATE LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION ANDEQUIPMENT SPECIFIC CONDITIONS

Theoperator shall comply with the terms and conditions setforth below: The test shall be conducted quarterly during the first 12 months after the initial source test, and once ayearthereafter. The District shall be notified of the date and time of the test at least 7 days pnor to the test. Source test shall be conducted when this equipment is using natural gas. The test shall be conducted by a testing laboratory certified by the California Air Resources Board in the required test methods , and in compliance with District Rule 304 (no conflict ofinterest). The test shall be conducted to determine the NH3 emissions usmg District method 207.1 measured over a 60 minute averaging time period. The test shall be conducted to determine the NH3 emissions using either District method 5.3 or EPA method 17 measured over a 60 minute averaging time period. The test shall be conducted when the equipment is operating at 80 percent load or greater. The test shall be conducted and the results submitted to the District within 45 days after the test date. 

### [RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition :C73, C75] D29.2 The operator shall conduct source test(s) for the pollutant(s) identified below. Pollutant(s) to be tested 

# IRequired Test Method(s) 

# IAveraging Time 

# I Test Location

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178



## FACILITYPERMITTOOPERATE Section D Page: 58 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall complywiththe terms and conditions set forth below: NH3 emissions District method 207.1 and 5.3 or EPA method 17 

# I 1hour 

# IOutlet ofthe SCR servingthis equipment
The test(s) shall be conducted at least once each calendar quarter during the first 12 months of operation and at least annually thereafter. The NOx concentration, as detennined by the CEMS, shall be simultaneously recorded during the ammonia slip test. If the CEMS is inoperable, a test shall be conducted to detennine the NOx emissions using District Method 100.l measured over a 60 minute averaging time period. The test shall be conducted to demonstrate compliance with the Rule 1303 concentration limit. The test shall be conducted when the equipment is operating at 80 percent load or greater. The test shall be conducted and the results submitted to the AQMD pennitting engineer within 45 days after the test date. The test shall be conducted during natural gas firing. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition : C131, C139] D29.4 The operator shall conduct source test(s) for the pollutant(s) identified below. Pollutant(s) to be tested SOX emissions Required Test Method(s) Approved District method 

# I Averaging Time District-approved averaging time 

# I Test Location Fuel sample

### South Coast Air Quality Management District 21865 Copley Drive. Diamond Bar, CA 91765-4178



## FACILITY PERMITTOOPERATE Section D Page: 59 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY, DWPHAYNES GENERATINGSTATION

SECTION D: FACILITY DESCRIPTION ANDEQUIPMENT SPECIFIC CONDITIONS
The operatorshall comply with theterms and conditions set forth below: ROG emissions 

### PMIO emissions Approved District method District method 5.2 I hour District-approved averaging time The test(s) shall be conducted at least once every three years. 

# IOutlet ofthe SCR serving this equipment 

# IOutletofthe SCR

serving this equipment

For gas turbines only the VOC test shall use the following method: a) Stack gas samples are extracted into Summa canisters, maintaining a final canister pressure between 400-500 mm Hg absolute, b) Pressurization of Summa canisters is done with zero gas analyzed/certified to having less than 0.05 ppmv total hydrocarbons as carbon, and c) Analysis of Summa canisters is per EPA Method T0-12 (with pre-concentration) and the canisters temperature when extracting samples for analysis is not to be below 70 deg F. The use of this alternative VOC test method is solely for the determination of compliance with the VOC BACT level of 2.0 ppmv calculated as carbon for natural gas fired turbines. Because the BACT level was set using data derived from various source test methods, this alternate method provides a fair comparison and represents the best sampling and analysis technique for this purpose at this time. The test results must be reported with two significant digits. The test shall be conducted and the results submitted to the AQMD within 60 days after the test date. The AQMD shall be notified of the date and time of the test at least 7days prior to the test. The test shall be conducted to demonstrate compliance with the Rule 1303 concentration and emissions limit. The test shall be conducted when the turbine and duct burner are operating simultaneously at I00 percent of full rated load, when the turbine is operating alone at I00 percent of full rated load, and when the turbine is operating alone at 75 and 50 percent offull rated load forNOx, CO, ROG, and NH3 source tests. The test shall be conducted when firing natural gas.

## South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 60 Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall comply with the terms and conditions set forth below:
[RULE 1303(a)(1)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] [Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] D29.5 The operator shall conduct source test(s) for the pollutant(s) identified below. Pollutant(s) to be tested NOX emissions Required Test Method(s) District method 100.1 

# IAveraging Time 30 minutes 

# I TestLocation Outlet ofthe SCR serving this equipment The test shall be conducted when the unit is firing diesel fuel in order to determine the emissions profile of the unit. A minimum of 6 tests shall be performed and the operator shall record the turbine output, ammonia injection rate, and temperature of the exhaust during each test, based on a 30 minute averaging time. Test results shall also include the fuel flow rate (CFH), the flue gas flow rate, and the duct burner fuel use during the test. The test shall be conducted in order to generate a load curve for NOx (lbs/MW) vs. MW output over the span of tested loads. The operator may, after receiving approval from the AQMD, use this curve to report NOx emissions during the monthly 60 minute (total) diesel readiness testing periods. [RULE 2012, 5-6-2005] [Devices subject to this condition: Dl25, D129, Dl34, Dl42] D29.7 The operator shall conduct source test(s) for the pollutant(s) identified below.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 61 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTIOND: FACILITYDESCRIPTIONANDEQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywiththeterms and conditions setforth below: Pollutant(s) to Required Test Method(s) Averaging Time 

# I Test Location be tested SOX emissions Approved District method I hour Fuel Sample 

## voe emissions Approved District method I hour Outlet ofthe SCR servingthis equipment PMIO Approved District method District-approved 

# IOutlet ofthe SCR emissions averaging time servingthis equipment PM2.5 Approved District method District-approved 

# IOutlet ofthe SCR averaging time servingthis equipment The test(s) shall be conducted at leastonce every three years. The test shall be conducted and the results submitted to the District within 90 days after the test date. The AQMD shall be notified of the date and time of the test at least I0days prior to the test
.. The test shall be conducted when the gas turbine is operating at I00 percent of maximum heat input.. For gas turbines only the VOC test shall use the following method: a) Stack gas samples are extracted into Summa canisters, maintaining a final canister pressure between 400-500 mm Hg absolute, b) Pressurization of Summa canisters is done with zero gas analyzed/certified to having less than 0.05 ppmv total hydrocarbons as carbon, and c) Analysis of Summa canisters is per EPA Method T0-12 (with pre-concentration) and the canisters temperature when extracting samples for analysis is not to be below 70 degrees The use of this alternative VOC test method is solely for the determination of compliance with the VOC BACT level of 2.0ppmv calculated as carbon for natural gas fired turbines. The test results must be reported with two significant digits. The test shall be conducted to demonstrate compliance with the Rule 1303 concentration and/or monthly emissions limit.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Section D Page: 62 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY, DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS

The operator shall comply with the terms and conditions set forth below: [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1303(b)(2)-0ffset,5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002] [Devices subjecttothis condition: Dl59,Dl65, DI71, DI77, Dl83, Dl89] D29.8 The operator shall conduct source test(s) for the pollutant(s) identified below. Pollutant(s) to be tested NH3 emissions Required Test Method(s) District method 207.1 or EPA method 17 Averaging Time I hour 

# I TestLocation Outletofthe SCR serving this equipment The test shall be conducted and the results submitted to the District within 90 days after the test date. The AQMD shall be notified of the date and time of the test at least I0 days priortothe test.. The test(s) shall be conducted at least quarterly during the first twelve months of operation and at least annually thereafter. The NOx concentration, as determined by the certified CEMS, shall be simultaneously recorded during the ammonia slip test. If the CEMS is inoperable or not yet certified, a test shall be conducted to determine the NOx emissions using District Method I00.1 measured over a 60 minute averaging time period

.. The test shall be conducted to demonstrate compliance with the Rule 1303 concentration limit.. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subjecttothiscondition: C73, C75, Cl62,Cl68,Cl74,Cl80,Cl86, Cl92] D82.I The operator shall install and maintain a CEMS to measure the following parameters:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 63 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWP HAYNES GENERATING STATION

SECTION D: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywiththeterms and conditions setforth below:
COconcentration in ppmv Concentrations shall be corrected to 15 percent oxygen on a dry basis. The CEMS will convert the actual CO concentrations to mass emission rates (lbs/hr) and record the hourly emission rates on a continuous basis. The CEMS shall be installed and operated no later than 90 days after initial start up of the turbine, and in accordance with an approved AQMD Rule 218 CEMS plan application. The operator shall not install the CEMS prior to receiving initial approval from AQMD. Within two weeks of the turbine start up date, the operator shall provide written notification to the AQMD ofthe exact start up. The CEMS shall be installed and operated to measure CO concentration over a 15 minute averagingtime period. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 218, 8-7-1981; RULE 218, 5-14-1999) [Devices subjectto this condition: 0125, 0129, 0134, 0142) 082.2 The operator shall install and maintain a CEMS to measure the following parameters: NOX concentration in ppmv Concentrations shall be corrected to 15 percent oxygen on a dry basis. The CEMS shall be installed and operated no later than 12 months after initial start up of the turbine and shall comply with the requirements of Rule 2012. During the interim period between the initial start up and the provisional certification date of the CEMS, the operator shall comply with the monitoring requirements of Rule 2012(h) (2) and 2012(h)(3). Within two weeks prior to the turbine start up date, the operator shall provide written notification to the AQMD ofthe exact date ofstartup.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 64 F'acilitv ID: 800074 Revision#: 28 Date: January 14,2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall comply with the terms and conditions set forth below: [RULE 2012, 5-6-2005] [Devices subject to this condition: 0125, 0129, 0134, 0142] 082.3 The operator shall install and maintain a CEMS to measure the following parameters: CO concentration in ppmv Concentrations shall be corrected to 15 percent oxygen on a dry basis. The CEMS shall be installed and operated to measure CO concentration over a 15 minute averaging time period. The CEMS shall be installed The CEMS shall be operated m accordance with an approved AQMO Rule 218 CEMS plan application. The CEMS will convert the actual CO concentrations to mass em1ss10n rates (lbs/hr) and record the hourly emissionrates on a continuous basis. CO Emission Rate, lbs/hr = K*Cco*Fd[20.9/(20.9%

- %02d)][(Qg 

## * HHV)/106], where

I. K = 7.267 

## *l0-8 (lb/sct)/ppm 2. Ceo = Average offour consecutive 15 min. average CO concentration, ppm 3. Fd = 8710 dscf/MMBTU natural gas 4. %02d =Hourly average%by vol. 02dry, corresponding to Ceo 5. Qg =Fuel gas usage duringthe hour, scf/hr 6. HHV = Gross high heating value offuel gas, BTU/scf [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 218, 8-7-1981; RULE 218, 5-14-1999]

### South Coast Air Quality Management District 21865 Copley Drive. Diamond Bar, CA 91765-4178



## FACILITYPERMIT TOOPERATE Section D Page: 65 Facility ID: 800074 Revision#: 28 Date: January 14,2015



## LA CITY, DWP HAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

The operatorshall complywith the terms and conditions setforth below: [Devices subject to this condition: Dl59, Dl65, Dl71, DI77, Dl83,Dl89] D82.4 The operator shall install and maintain a CEMS to measure the following parameters: NOX concentration in ppmv Concentrations shall be corrected to 15 percent oxygen on a dry basis. The CEMS shall be installed and operated no later than 90 days after initial start-up of the turbine, and in accordance with an approved AQMD Rule 218 CEMS plan application. The operator shall not install the CEMS prior to receiving initial approval fromAQMD. [RULE 2012,5-6-2005] [Devices subject to this condition: Dl59, D165, D171, DI77, Dl83, Dl89] Dl82.l The operator shall testthis equipment in accordance with the following specifications:
The operator shall collect samples using a 1983 District-approved induct fallout monitor (!FM) every 24 hours beginning from all startups, except for natural gas firing, where if three 24-hour !FM samples show no abnormal collection, subsequent samples can be taken once a week. The operator shall analyze the !FM samples for acidity, weight, increase of particle size, volume, and appearance, and use the results of the analysis to determine the necessary operational changes to minimize the fallouts, such as, but not limited to, increasing the fuel oil additives and lancing frequencies. [RULE 401, 3-2-1984; RULE 401, 11-9-2001] [Devices subject to this condition: DI, D4]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 66 Facility ID: 800074 Revision #: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTIOND: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall complywiththeterms andconditions set forth below:

0322.1 The operator shall perform annual inspection of the equipment and filter media for leaks, broken ortom filter media, and improperly installed filter media. [RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subject to this condition : E112]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 67 Facilitv ID: 800074 Revision#: 28 Date: January 14,2015



## LA CITY,DWP HAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION ANDEQUIPMENT SPECIFIC CONDITIONS
The operatorshallcomplywith theterms and conditions setforth below:

D323.l The operator shall conduct an inspection for visible emissions from all stacks and other emission points of this equipment whenever there is a public complaint of visible emissions, whenever visible emissions are observed, and on a daily basis, at least, unless the equipment did not operate during the entire daily period. The routine daily inspection shall be conducted whilethe equipment is in operation and during daylight hours. If any visible emissions (not including condensed water vapor) are detected that last more than three minutes in any one hour, the operator shall verify and certify within 24 hours that the equipment causing the em1ss1on and any associated air pollution control equipment are operating normally according to their design and standard procedures and underthe same conditions underwhich compliance was achieved in the past, and either: 1 ). Take corrective action(s) that eliminates the visible emissions within 24 hours and report the visible emissions as a potential deviation in accordance with the reporting requirements in Section Kofthis permit; or 2). Have a CARE-certified smoke reader determine compliance with the opacity standard, using EPA Method 9 or the procedures in the CARB manual "Visible Emission Evaluation", within three business days and report any deviations to AQMD. SUGGESTED CHAR The operator shall keep the records in accordance with the recordkeeping requirements m Section Kofthis permit and the following records: I). Stack oremission point identification; 2). Description ofany corrective actions taken to abate visible emissions; 3). Date andtime visible emission was abated; and 4). All visible emission observation records by operator or a certified smoke reader.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-41 78



## FACILITYPERMITTO OPERATE Section D Page: 68 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY, DWPHA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS
The operator shall complywiththeterms and conditions set forth below: [RULE 3004(a)(4)-PeriodicMonitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subjectto this condition: C27, C28, C29, C30, C31, C32]

### South Coast Air Quality Management District Z1865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 69 Facility ID: 800074 Revision#: 28 Date: January 14. 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith the terms and conditions setforth below:

D323.2 The operator shall conduct an inspection for visible emissions from all stacks and other emission points of this equipment whenever there is a public complaint of visible emissions, whenever visible emissions are observed, and on a semi-annual basis, at least, unless the equipment did not operate during the entire semi-annual period. The routine semi-annual inspection shall be conducted while the equipment is in operation and during daylighthours. If any visible em1ss1ons (not including condensed water vapor) are detected that last more than three minutes in any one hour, the operator shall verify and certify within 24 hours that the equipment causing the em1ss1on and any associated air pollution control equipment are operating normally according to their design and standard procedures and underthe same conditions underwhich compliance was achieved in the past, and either: 1

). Take corrective action(s) that eliminates the visible emissions within 24 hours and report the visible emissions as a potential deviation in accordance with the reporting requirements in Section Kofthis permit; or 2). Have a CARB-certified smoke reader determine compliance with the opacity standard, using EPA Method 9 or the procedures in the CARB manual "Visible Emission Evaluation", within three business days and report any deviations to AQMD.
The operator shall keep the records in accordance with the recordkeeping requirements in Section Kofthis permit and the following records: 1 ). Stack oremission point identification; 2). Description ofany corrective actions taken to abate visible emissions; 3). Date and time visible emissionwas abated; and 4). All visible emission observation records by operator or a certified smoke reader.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 70 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

Theoperator shall complywith the terms and conditions set forth below: [RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subject to this condition :D56] D371.I The operator shall conduct an inspection for visible em1ss10ns from all stacks and other emission points of this equipment whenever this equipment has combusted one million gallons of diesel fuel, to be counted cumulatively over a five year period. The inspection shall be conducted while the equipment is in operation and during daylight hours. If any visible emissions (not including condensed water vapor) are detected, the operator shall: Have a CARS-certified smoke reader determine compliance with the opacity standard, using EPA Method 9 or the procedures in the CARB manual "Visible Emission Evaluation", within three working days (or during the next fuel oil firing period if the unit ceases firing on fuel oil within the three working day time frame) and report any deviations to AQMD. In addition, the operator shall keep the records in accordance with the recordkeeping requirements in Section K ofthis permit and the following records: a). Stack oremission point identification; b). Description ofany corrective actions taken to abate visible emissions; c). Date and time visible emission was abated; and d). Visible emission observationrecord by a certified smoke reader. [RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subjectto this condition: DI, 04]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 71 Facility ID: 800074 Revis.ion#: 28 Date: Janlllll)' 14, 2015



## LACITY,DWP HAYNES GENERATING STATION

SECTIOND: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywiththeterms and conditions set forth below:

0372.1 The operator shall determine compliance with the particulate matter (PM) em1ss1on limit by conducting a source test at the outlet of the exhaust stack annually using AQMD Method 5.1. Each test shall include: (a) One test using natural gas operating at mm1mum load under normal operating conditions, if natural gas is burned more than 120 consecutive hours or 200 hours accumulated over any 12 consecutive months. The test shall be conducted no later than six months afterthe time limit has been exceeded; (b) One test using natural gas operating at maximum load under normal operating conditions, if natural gas is burned more than 120 consecutive hours or 200 hours accumulated over any 12 consecutive months. The test shall be conducted no later than six months afterthe time limit has been exceeded; (c) One test using fuel oil operating at maximum load under normal operating conditions, if fuel oil is burned more than 120 consecutive hours or 200 hours accumulated over any twelve consecutive months. The test shall be conducted no later than six months after the time limit has been exceeded. [RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subject to this condition: 0125, 0129, 0134, 0142]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 72 Facility ID: 800074 Revision#: 28 Date: January 14. 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywith theterms and conditions set forth below:

D381.l The operator shall conduct an inspection for visible emissions from all stacks and other emission points of this equipment whenever there is a public complaint of visible em1ss10ns, whenever visible emissions are observed, and on an annual basis, at least, unless the equipment did not operate during the entire annual period. The routine annual inspection shall be conducted while the equipment is in operation and during daylight hours. If any visible emissions (not including condensed water vapor) are detected, the operator shall take corrective action(s) that eliminates the visible emissions within 24 hours and report the visible emissions as a potential deviation in accordance with the reportingrequirements in Section K ofthis permit. The operator shall keep the records in accordance with the recordkeeping requirements m Section K ofthis permit and the following records: 1

). Stack oremission point identification; 2). Description ofany corrective actions taken toabate visible emissions; and 3). Date and time visible emission was abated. [RULE 3004(a){4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subjectto this condition : E112] 

### E. EquipmentOperation/ConstructionRequirements E57.1 The operator shall vent this equipment to the SCR and CO control whenever this equipment is in operation. Ammonia injection shall be used at all times at an injection rate which minimizes NOx emissions whenever the exhaust temperature prior to the inlet of the SCR catalyst is 450 degrees F or greater as measured by the temperature gauge required by condition Dl2.6

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 73 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATINGSTATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith theterms and conditions set forth below:
[RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 4-20-2001; RULE 2005, 5-6-2005] [Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] E73.l Notwithstanding the requirements of Section E conditions, the operator shall not use ammonia injection ifany ofthe following requirement(s) are met: I. Whenever the inlet exhaust temperature prior to the SCR reactor is less than 530 degrees Fahrenheit. [RULE 2012, 5-11-2001; RULE 2012, 12-5-2003] [Devices subject to this condition :C73, C75] E73.2 Notwithstanding the requirements of Section E conditions, the operator may, at his discretion, choose not to use ammonia injection if all of the following requirement(s) are met: The inlet exhaust temperature to the SCR is 450 degrees F or less, not to exceed 360 minutes during a cold startup or 180 minutes during a non-cold startup. During diesel readiness testing. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 4-9-1999; RULE 2005, 4-20-2001] [Devices subject to this condition : C131, C139] E116.1 This engine shall not be used as part of a demand response program usmg interruptible service contract in which a facility receives a payment or reduced rates in return for reducing its electric load on the grid when requested to do so by the utility or the grid operator.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 74 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshall complywith theterms and conditions set forth below:
[RULE 1470, 6-1-2007] [Devices subject to this condition :D53] E116.2 This engine shall not be used as part of a demand response program using interruptible service contract in which a facility receives a payment or reduced rates in return for reducing its electric load on the grid when requested to do so by the utility or the grid operator. [RULE 1470, 5-4-2012] [Devices subjectto this condition : D195, D196] E144.1 The operator shall vent this equipment, during filling, only to the vessel from which it 1s being filled. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition :D34, D35, D36, D37, D38, D39] El79.l For the purpose of the following condition number(s), "continuous monitoring" shall be defined as measuring at least once every 15 minutes, except as allowed by Rule 2000. Condition Number D 12- 3
[RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition :C73, C75]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 75 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshallcomplywiththeterms and conditions set forth below:

El79.2 For the purpose of the following condition number(s), "continuously record" shall be defined as recording at least once every hour and shall be calculated based upon the average ofthe continuous monitoring for that hour. ConditionNumber D 12- 3
[RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 5-11-2001; RULE 2012, 12-5-2003] [Devices subject to this condition :C73, C75] El79.3 For the purpose of the following condition number(s), continuously record shall be defined as recording at least once every hour and shall be calculated upon the average of the continuous monitoring for that month. Condition Number D 12- 7
[RULE 1303(a){l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 5-11-2001; RULE 2012, 12-5-2003] [Devices subject to this condition : C131, C139] E179.4 For the purpose of the following condition number(s), continuously record shall be defined as recording at least once every hour and shall be calculated upon the average of the continuous monitoring for that hour. Condition Number D 12- 6 Condition Number D 12- 8 [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2012, 5-11-2001; RULE 2012, 12-5-2003]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 76 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITYDESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywiththe terms andconditions set forth below: [Devices subject to this condition : C13 1, C139] El79.5 For the purpose of the following condition number(s), continuously record shall be defined as recording at least once every 15 minutes and shall be calculated based upon the average ofthe continuous monitoring for that hour

.. ConditionNumber D 12- 9
[RULE 1303(a)(1)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1703 -PSDAnalysis, 10-7-1988; RULE 2005, 5-6-2005] [Devices subject to this condition: Cl62, Cl68,Cl74, Cl80,C!86, Cl92] El79.6 For the purpose of the following condition number(s), continuously record shall be defined as at least once every hour and shall be calculated based upon the average of the continuous monitoring for that month. ConditionNumber D 12-10 Condition Number D 12-11 [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 2005, 5-6-2005] [Devices subject to this condition : C162, C168, Cl74, Cl80,C186, Cl92] E193.l The operator shall upon completion of construction, operate and maintain this equipment according to the following specifications: Jn compliance with all mitigation measures as stipulated by the "Statement of Findings, Statement of Overriding Considerations, and Mitigation Monitoring Plan" and final Environmental Impact Report dated July 16, 2002 (SCH No. 20011121013), and addendum to the FEIR

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 77 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY, DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywiththeterms and conditions set forth below: [CA PRC CEQA, 11-23-1970] [Devices subjecttothis condition: 0125, 0129, 0134, 0142] El93.6 The operator shall upon completion of construction, operate and maintain this equipment according to the following specifications: In accordance with all air quality mitigation measures stipulated in the Environmental Impact Report (EIR), State Clearing House#2005061111. [CA PRC CEQA, 11-23-1970] [Devices subject to this condition 0196] 0159, 0165, 0171, 0177, 0183, 0189, 0195,
El93.7 The operator shall operate and maintain this equipment according to the following requirements: The gas turbines shall operate with natural gas exclusively. The operator shall vent this equipment to the CO oxidation catalyst and SCR control system whenever the turbine is in operation. Written records of commissioning, startups, and shutdowns shall be maintained and made available upon request from AQMD. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1303(b)(2)-0ffset, 5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002; RULE 1703 -PSD Analysis, 10-7-1988; RULE 2005, 5-6-2005] [Devices subject to this condition: 0159, 0165, 0171, DI77, 0183, 0189] El93.9 The operator shall operate and maintain this equipment according to the following requirements:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Section D Page: 78 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

The operator shall complywith the terms and conditions set forth below:
The operator shall calculate and continuously record the NH3 slip concentration using the following equation NH3 (ppmvd) = [a-b*(c*l.2)/l,OOO,OOO]*l,000,000/b where a=NH3 injection rate (lb/hr)/l7(1b/lb-mol), b= dry exhaust flow rate (scf/hr)/ (385.5 scf/lb-mol), c = change in measured NOx across the SCR, ppmvd at 15 percent 02. The operator shall install a NOx analyzer to measure the SCR inlet NOx ppm accurate to within +/- 5percent calibrated at least once every 12 months. The operator shall use the method described above or another alternative method approved by the Executive Officer. The ammonia slip calculation procedures described above shall not be used for compliance determination or emission information determination without corroborative data using an approved reference method for the determination of ammonia. The ammonia slip calculation procedure shall be in-effect no later than 90 days after initial startup ofthe turbine. [RULE 1303(a)(l)-BACT, 5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002] [Devices subject to this condition: Cl62, Cl68, Cl74, Cl80,Cl86, Cl92] El93.IO The operator shall operate and maintain this equipment according to the following requirements:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Facilitv ID: Revision#: Page: 79 800074 28 Date: January 14, 2015



## LA CITY, DWP HAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith theterms and conditions set forth below: The operator shall not commence operation of any of the new Units 11-16 until the AQMD certifies that one ofthe following conditions has been satisfied: A, The facility has provided 292 lbs/day of federally enforceable PM2.5 emission reduction credits unless a different amount associated with the Repower Project modification at this facility as determined to be required according to the federal New Source Review (NSR) requirements (40CFR Part 51 Subpart Z Appendix S), as approved by both AQMD and EPA. 

### B. The operator shall comply with a federally enforceable limit of JOO tons per year ofPM2.5 emissions. For purposes of demonstrating compliance with the I00 ton per year limit the operator shall determine the PM2.5 emissions for each of the major sources at the facility by calculating a 12-monthrolling average usingthe following formula: PM2.5 = (FF!*EFI+ FF2*EF2+ FF9*EF9+ FFIO*EFIO+ FFll*EFll+ FFl2*EF12+ FF13*EFl3+ FF14*EFl4+ FFl5*EFl5+ FFl6*EFl6+FFDI*EFDI+FFD2*EFD2)/2000 Where: PM2.5 = PM2.5 emissions in tons per year, FFI= fuel flow for Unit I in MMscf, FF2= fuel flow for Unit 2 in MMscf, FF9= fuel flow for Unit 9 in MMscf, FFIO= fuel flow for Unit JO in MMscf, FFI I to FFl6= fuel flow for Units 11 to 16 in MMscf, FFDI to FFD2 = diesel usage for two black start generator in Mgal. EF!= emission factor for Unit I= 7.14 lb/MMscf, EF2= emission factor for Unit 2 6.61 lb/MMscf, EF9= em1ss1on factor for Unit 9 = l.238 lb/MMscf, EFIO= emission factor for Unit 10 = 0.968 lb/MMscf, EFII to EF16 = emission factor for Units 11 to 16 = 6.423 lb/MMscf, EFDl to EFD2 = emission factor for two standby generators= 0.32 lb/Mgal. Any changes to these emission factors must be approved in advance by the District in writing and be based on unit specific source tests performed usmg a District approved testing protocol.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 80 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

The operatorshallcomply with the terms and conditions set forth below: [40CFR Part51, Appendix S, 10-20-2010] [Devices subject to this condition : Dl59, Dl65, 0171, Dl77, Dl83, 0189, D195, Dl96] E193.l l The operator shall operate and maintain this equipment according to the following requirements: a. CHANGE OIL AND FILTER EVERY 500 HOURS OF OPERATION OR ANNUALLY, WHICHEVER COMES FIRST. b. INSPECT ANNUALLY, AND AIR CLEANER EVERY 1,000 HOURS OF OPERATION OR WHICHEVER COMES FIRST, AND REPLACE AS NECESSARY;

c. INSPECT ALL HOSES AND BELTS EVERY 500 HOURS OF OPERATION OR ANNUALLY, WHICHEVER COMES FIRST, AND REPLACE AS NECESSARY. 

### [40CFR 63 Subpart

### ZZZZ, 1-30-2013] [Devices subjectto this condition :053] E202.l The operator shall clean and maintain this equipment according to the following specifications: The operator shall wash and/or vacuum and then inspect the boiler ducts, stack, and air preheaters during each shutdown in which a boiler is cooled. The operator shall reinspect and perform additional cleaning onthese areas as necessary priorto startup. The operator shall install and maintain a permanent stack washing system in the boiler stack The operator shall wash the stack prior to start-up each time the boiler is shut down for 48 hours ormore

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Facilltv ID· Revision#: Page: 81 800074 28 Date: January 14. 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomply withtheterms and conditions setforth below: [RULE 401,3-2-1984; RULE 401, 11-9-2001] [Devices subject to this condition: DI, D4] E204.I The operator shall employ the fuel oil additive system according to the following specifications: The operator shall inject District-approved additives at a rate between 6,500 and 10,500 parts ofoil perpart ofadditive, based on volume. The operator shall inject District-approved additives into the fuel oil whenever fuel oil is burned, as soon as fuel oil firing has stabilized. The operator shall take corrective action as expeditiously as practicable if there is a failure to comply with either of the above requirements, so that compliance is achieved within 48 hours of such failure; the operator shall switch the unit to natural gas fuel, provided such fuel is available, if such failure is longer than 48 hours, and will remain on natural gas until such time as the failure is corrected. The operator shall check the flow of fuel oil additive at least once a shift by recording the level ofthe additive in the holdingtank. [RULE 401, 3-2-1984; RULE 401, 11-9-2001] [Devices subject to this condition : DI, D4] E204.2 The operator shall perform a boiler lancing according to the following specifications:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Section D Page: 82 Facility ID: 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITYDESCRIPTION ANDEQUIPMENT SPECIFIC CONDITIONS

The operatorshall complywith the terms and conditions set forth below: The operator shall cycle the boiler and air preheater lancing continuously while burning fuel oil and shall commence as soon as oil firing has stabilized; the operator shall continue the lancing cycle for the first 24 hours following a change from fuel oil to natural gas. The operator shall cycle the air preheater lances and boiler lances once daily and once weekly, respectively, during periods ofnatural gas burning. The operator shall repair and return to services individual lances as soon as practicable; the operator shall switch the unit to natural gas, provided such fuel is available, in the event that five or more lances are out of service simultaneously for more than 48 hours, and shall keep the unit on natural gas until such time as the repairs have been completed sothat no more than two lances remain out ofservice. [RULE 401, 3-2-1984; RULE 401, 11-9-2001) [Devices subject to this condition :DI, 04) E448.I The operator shall comply withthe following requirements:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 83 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomply withthe terms and conditions set forth below: The engine and the Johnson Matthey CRT+ diesel particulate filter shall be operated in accordance with CARB Executive Order DE-08-009-04. The engine shall operate at the load level required to achieve 240 0C for a mmtmum of 40% of the engine's operating time and a NOx/PM ratio of 15 @ >= 300 0C and 20 @ <= 3000C. The NOx/PM ratio shall be at least 8 with a preference for 20 or higher. The engine shall not operate below passive regeneration temperature for more than 720 consecutive minutes. Regeneration is required after 24 consecutive cold starts and 30-minute idle sessions. Filter cleaning is required after 150 half-hour cold starts with associated regeneration or 1000 hours of emergency use. The CRTdm, which monitors engine exhaust back pressure and temperature will determine the actual cleaning interval and provide an alert when filter cleaning is required. The operator shall keep records of any corrective action taken after the CRTdm has notified the operatorthat a high pressure limit is reached. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1470, 5-4-2012] [Devices subject to this condition : D195, D196] E448.2 The operator shall comply with the following requirements:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar. CA 91765-4178 Section D Facilitv ID: Page: 84 800074 Revision#: 28 Date: January 14, 2015 

## FACILITYPERMITTO OPERATE LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTIONAND EQUIPMENT SPECIFIC CONDITIONS

The operator shall complywith theterms and conditions 

### set forth below: Removal of the diesel particulate filter's filter media for cleaning may only occur underthe following conditions: A. The internal combustion engine shall not be operated for maintenance and testing or any other non-emergency use while the diesel particulate filter media is removed; and B. The diesel particulate filter's filter media shall be returned and re-installed within 10 working days from the date ofremoval; and C. The owner or operator shall maintain records indicating the date(s) the diesel particulate filter's filter media was removed for cleaning and the date(s) the filter media was re-installed. Records shall be retained for a minimum period of 36 months. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1470, 5-4-2012] [Devices subject to this condition : D195, D196] E448.3 The operator shall comply with the following requirements:
The engine shall comply with the emission standards specified in 40 CFR 60.4204(b) and 4205(b). The operator must comply by purchasing an engine certified to the emission standards in 40CFR 60.4204(b), or 4205(b) or (c), as applicable, for the model year and maximum engine power. The engine must be installed and configured according tothe manufacturer's specifications. The engine and the control device shall be operated and maintained in accordance with the manufacturer's written emission-related instructions or procedures developed by the operator that are approved by the engine manufacturer. Changes to those emission-related settings that are setby the manufacturer are not allowed.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Section D Page: 85 Facilitv ID: 800074 Revision#: 28 Date: January 14. 2015



## LA CITY, DWPHA YNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshallcomplywith the terms andconditions set forth below: [40CFR 60 Subpart IITI, 7-11-2006] [Devices subject to this condition :D l9S, D196] 

### H. 

### Applicable Rules H23.l This equipment is subject to the applicable requirements of the following rules or regulations: Contaminant Rule Rule/Subpart 

## voe District Rule 463 [RULE 463, 3-11-1994] [Devices subject to this condition: D46, D47, D48, D49, DSO] H23.3 This equipment is subject to the applicable requirements of the following rules or regulations: Contaminant Rule Rule/Subpart 

## voe District Rule 464 [RULE 464, 12-7-1990] [Devices subject to this condition : Dll6, Dll7, Dll8, Dll9, Dl20, 0122, Dl23, DIS4, DISS] H23.S This equipment is subject to the applicable requirements of the following rules or regulations: Contaminant Rule Rule/Subpart

## South Coast Air Quality Management District Z1865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section D Page: 86 Facilitv ID: 800074 Revision#: 28 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRJPTION ANDEQUIPMENT SPECIFIC CONDITIONS

The operatorshallcomplywith theterms and conditions set forth below: Refrigerants 

# IDistrict Rule 

# I 1415 [RULE 1415, 10-14-1994] [Devices subjectto this condition : E113] H23.6 This equipment is subject to the applicable requirements of the following rules or regulations: Contaminant Refrigerants Refrigerants Rule 40CFR82, SUBPART District Rule Rule/Subpart B 1411 [RULE 1411, 3-1-1991; 40CFR82 SubpartB, 7-14-1992] [Devices subject to this condition : E114] K. Record Keeping/Reporting K40.3 The operator shall provide to the District a source test report in accordance with the following specifications:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar. CA 91765-4178



## FACILITYPERMIT TO OPERATE Section D Page: 87 Facility ID· 800074 Revision#: 28 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

The operator shall complywith the terms and conditions setforth below: Source test results shall be submitted to the District no later than 60 days after the source testwas conducted. Emission data shall be expressed in terms of concentration (ppmv), corrected to 15 percent oxygen, dry basis. All exhaust flow rate shall be expressed in terms of dry standard cubic feet per minute (DSCFM) and dry actual cubic feet per minute (DACFM). All moisture concentration shall be expressed in terms of percent corrected to 15 percent oxygen. Emission data shall be expressed in terms of mass rate (lbs/hr). In addition, solid PM emissions, if required to be tested, shall also be reported in terms of grains per DSCF. Source test results shall also include fuel flow and exhaust gas rate under which the test was conducted. Source test results shall also include turbine and generator output under which the testwas conducted. Emission data shall be expressed in terms oflbs/MM cubic feet. [RULE 1303(a)(l)-BACT,5-10-1996; RULE 1303(a)(l)-BACT, 12-6-2002; RULE 1303(b)(2)-0ffset,5-10-1996; RULE 1303(b)(2)-0ffset, 12-6-2002; RULE 2005, 4-9-1999; RULE 2005,4-20-2001] [Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] K67.l The operator shall keep records, in a manner approved by the District, for the following parameter(s) or item(s):

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section D Page: 88 Facility JD· 800074 Revision#: 28 Date· January 14. 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall complywith theterms and conditions set forth below: the name of the person perfonning the inspection and/or maintenance of the dust collector the date, time and results ofthe inspection the date, time and description of any maintenance or repairs resulting from the inspection [RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subject to this condition : E112] K67.2 The operator shall keep records, in a manner approved by the District, for the following parameter(s) or item(s): The operator shall monitor and record on a daily basis the flowrate of the incoming scrubbing (city) waterwhen this scrubber is operated [RULE 3004(a)(4)-PeriodicMonitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subject tothis condition :C40, C4l] K67.3 The operator shall keep records, in a manner approved by the District, for the following parameter(s) or item(s):

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Facilitv ID: Page: 89 800074 Revision#: 28 Date: January 14,2015 

## FACILITYPERMITTOOPERATE LA CITY, DWP HAYNES GENERATINGSTATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
Theoperatorshall comply withtheterms and conditions setforth below: For architectural applications where no thinners, reducers, or other VOC containing materials are added, maintain semi-annual records for all coating consisting of (a) coating type, (b) voe content as supplied in grams per liter (g/l) of materials for low-solids coatings, (c) voe content as supplied in g/I of coating, less water and exempt solvent, for other coatings. For architectural applications where thinners, reducers, or other VOC containing materials are added, maintain daily records for each coating consisting of (a) coating type, (b) voe content as applied in grams per liter (g/l) of materials used for low-solids coatings, (c) voe content as applied in g/I of coating, less water and exempt solvent, for other coatings. [RULE 3004(a)(4)-Periodic Monitoring, 8-11-1995; RULE 3004(a)(4)-Periodic Monitoring, 12-12-1997] [Devices subject to this condition : E124] K67.4 The operator shall keep records, in a manner approved by the District., for the following parameter(s) or item(s): Natural gas and Diesel fuel usage after eEMScertification. The date, time, duration, and CEMS minute data for start-ups. These records shall be maintained and made available upon request from AQMD [RULE 2012, 5-6-2005] [Devices subject to this condition: Dl25, Dl29, Dl34, Dl42] K67.5 The operator shall keep records, in a manner approved by the District, for the following parameter(s) or item(s):

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Facility ID· Revision#: Page: 90 800074 28 Date: January 14. 2015 

## FACILITYPERMIT TO OPERATE LA CITY,DWPHAYNES GENERATING STATION

SECTION D: FACILITY DESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS

Theoperatorshall complywith the terms and conditions set forth below: Date of operation, the elapsed time, in hours, and the reason for operation. Records shall be kept and maintained on file for a minimum of two years and made available to district personnel upon request. An engine operating log listing on a monthly basis the emergency use hours of operation, maintenance and testing hours of operation, and any other hours of use with a description of the reason for operation. Additionally, each time the engine is started manually, the log shall include the date of operation and the timer reading in hours at the beginning and end ofoperation. The log shall be kept for a minimum of three calendar years prior to the current year and be made available to District personnel upon request. The total hours of operation for the previous calendar year shall be recorded sometime during the first 15 days of January ofeach year. [RULE 1110.2,2-1-2008; RULE 1304(a)-Modeling and OffsetExemption,6-14-1996; RULE 1470, 6-1-2007] [Devices subjectto this condition :D53] K67.6 The operator shall keep records, in a manner approved by the District, for the following parameter(s) or item(s): Natural gas fuel use during the commissioning period
[RULE 2012,5-6-2005] [Devices subject to this condition: D159, Dl65, DI71, DI77, D183, DI 89] K67.7 The operator shall keep records, in a manner approved by the District, for the following parameter(s) or item(s):

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section D Facilitv ID: Page: 91 800074 Revision#: 28 Date: January14.2015 

## FACILITYPERMITTOOPERATE LACITY, DWPHAYNES GENERATING STATION

SECTION D: FACILITYDESCRIPTION AND EQUIPMENT SPECIFIC CONDITIONS
The operatorshallcomplywiththeterms and conditions setforth below: The operator shall keep a log of engine operations documenting the total time the engine is operated each month and the specific reason for operation as: A) Emergency Use, B) Maintenance and Testing, orC) Other (be specific) In addition, for each time the engine is manually started, the log shall include the date of engine operation, the specific reason for operation, and the totalizing hour meter reading (in hours and tenths ofhours) atthe beginning and the end ofthe operation. On or before January 15th of each year the operator shall record in the engine operating log: A) the total hours of engine operation for the previous calendar year, and B) the total hours of engine operation for maintenance and testing for the previous calendar year. Records shall be kept and maintained on file for a mm1mum of five years and made available to district personnel upon request. [RULE 1304(c)-OffsetExemption, 6-14-1996; RULE 1470, 5-4-2012; RULE 3004(a)(4) -PeriodicMonitoring, 12-12-1997; 40CFR60 SubpartIlll, 7-11-2006] [Devices subjectto this condition: Dl95,Dl96] Kl71.1 The operator shall notify the District ifany ofthe following situations occur: When fuel oil is fired in this equipment This notification shall be provided to the District no later than 48 hours after fuel oil is fired in this boiler. [RULE 401, 3-2-1984; RULE 401, 11-9-2001] [Devices subject to this condition: DI, 04]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178



## FACILITYPERMIT TO OPERATE Section E Page: I Facilitv ID: 800074 Revision#· 16 Date: January 14, 2015



## LA CITY,DWPHA YNES GENERATING STATION

SECTION E: ADMINISTRATIVE CONDITIONS The operating conditions in this section shall apply to all permitted equipment at this facility unless superseded by condition(s) listed elsewhere in this permit. I. The permit shall remain effective unless this permit is suspended, revoked, modified, reissued, denied, or it is expired for nonpayment ofpermitprocessing or annual operating fees. [201, 203, 209, 301]
a. The permit must be renewed annually by paying annual operating fees, and the permit shall expire ifannual operating fees are not paid pursuant to requirements ofRule 30l(d). [30l(d)] b. The Permitto Construct listed in Section H shall expire one year from the Permit to Construct issuance date, unless a Permit to Construct extension has been granted by the Executive Officer orunless the equipmenthas been constructed and the operator has notifiedthe Executive Officerprior to the operation ofthe equipment, inwhich case the Permit to Construct serves as a temporary Permitto Operate. [202, 205]
c. The Title V permit shall expire as specified under Section K ofthe Title V permit. The permit expirationdate ofthe Title V facility permit does not supercede the requirements ofRule 205. [205, 3004] 2. The operator shall maintain all equipment in such a mannerthat ensures proper operation ofthe equipment. [204] 3. This permit does not authorize the emissions ofair contaminants in excess ofthose allowedby Division 26 ofthe Health and Safety Code ofthe State ofCalifornia or the Rules and Regulations ofthe SCAQMD. This permit cannot be considered as permission to violate existing laws, ordinances, regulations, or statutes ofother governmental agencies. [204] 4. The operator shall notuse equipment identified inthis facility permit asbeing connected to airpollution control equipment unless they are so vented to the identified air pollution control equipmentwhich is in full use andwhich has been included in this permit. [204]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Section E Page: 2 Facilitv ID: 800074 Revision#: 16 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION E: ADMINISTRATIVE CONDITIONS

5. The operator shall not use any equipment having airpollution control device(s) incorporated within the equipment unless the airpollution control device is infull operation. [204] 6. The operator shall maintainrecords to demonstrate compliance with rules orpermit conditions that limit equipment operating parameters, orthe type or quantity of material processed. These records shall be made available to SCAQMDpersonnel upon request and be maintained for at least: [204]
a. Three years for a facility not subject to Title V; or b. Five years for a facility subject to Title V. 7. The operator shall maintain and operate all equipment to ensure compliance with all emission limits as specified inthis facility permit. Compliance with emission limits shall be determined according to the following specifications, unless otherwise specified by SCAQMDrules orpermit conditions: [204]
a. For internal combustion engines and gas turbines, measured concentrations shall be corrected to 15 percent stack-gas oxygen content on a dry basis and be averaged overa period of 15 consecutive minutes; [1110.2, 1134, 204] b. For other combustion devices, measured concentrations shall be corrected to 3 percent stack-gas oxygen contentona dry 

### basis and be averaged overa period of 15 consecutive minutes; [1146, 1146.1, 204]
c. For a large NOx source, compliance with a RECLAIM concentration limit shall be measured over a continuous 60 minutes for that source; [2012] d. Fornon-combustion sources, compliance with emission limits shall be determined and averaged overa period of60 minutes; [204]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar. CA 91765-4178



## FACILITYPERMITTO OPERATE Section E Page: 3 Facility ID: 800074 Revision#: 16 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION

SECTION E: ADMINISTRATIVE CONDITIONS

e. Forthe purpose ofdetermining compliance with Rule 407, carbon monoxide (CO) shall be measured on a dry basis and be averaged over IS consecutive minutes, and sulfur compoundswhichwould exist asliquid orgas at standard conditions shall be calculated as sulfur dioxide (S02)and be averaged over IS consecutive minutes; [ 407] f. Forthe purpose ofdetermining compliance with Rule 409, combustion contaminantemissionmeasurements shall be corrected to 12 percent ofcarbon dioxide (C02) at standard conditions and averaged over IS consecutive minutes. [ 409] g. Forthe purpose ofdetermining compliance with Rule 475, combustion contaminant emission measurements shall be corrected to 3 percent ofoxygen (02) at standard conditions and averaged over IS consecutive minutes or any otheraveraging time specifiedby the Executive Officer. [475] 8. All equipment operating underthe RECLAIM program shall comply concurrently with all SCAQMD Rules and Regulations, exceptthose listed inTable I ofRule 2001 for NOxRECLAIM sources and Table 2 ofRule 2001 for SOx RECLAIM sources. Those provisions listed in Tables 1or 2 shall not apply to NOx or SOx emissions afterthe date the facility has demonstrated compliance with all monitoring and reporting requirements ofRules 2011 or2012, as applicable. Provisions ofthe listed SCAQMDrules in Tables 1

### or2 which have initial implementation dates in 1994 shall not apply to a RECLAIM NOxor SOx source, respectively. [200l] 9. The operator shall, when a source test is required by SCAQMD,provide a source testprotocol to SCAQMD no laterthan 60 days before the proposed test date. The test shall not commence until the protocol is approved by SCAQMD. The test protocol shall containthe following information: [204, 304]
a. Briefdescription ofthe equipmenttested.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section E Page: 4 Facilitv ID: 800074 Revision#: 16 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION

SECTION E: ADMINISTRATIVE CONDITIONS

b. Briefprocess description, including maximum and normal operating temperatures, pressures, through-put, etc. c. Operating conditions under which the test will be performed. d. Method ofmeasuring operating parameters, such as fuel rate and process weight. Process schematic diagram showing the ports and sampling locations, including the dimensions ofthe ducts/stacks atthe sampling locations, and distances offlow disturbances, (e,g. elbows, tees, fans, dampers) from the sampling locations (upstream and downstream).
e. Briefdescription of.sampling and analytical methods used to measure each pollutant, temperature, flow rates, andmoisture. 

### £ Description ofcalibration and quality assurance procedures. g. Determinationthat the testing laboratory qualifies as an "independenttesting laboratory" under Rule 304 (no conflict ofinterest). l

### O. 

### The operator shall submit a report no laterthan 60 days after conducting a source test, unless otherwise required by SCAQMD Rules or equipment-specific conditions. The report shall contain the following information: [204]
a. The results ofthe source test. b. Briefdescription ofthe equipment tested.
c. Operating conditions under which test will be performed. d. Method ofmeasuring operating parameters, such as fuel rate and process weight. Process schematic diagram showing the ports and sampling locations, including the dimensions ofthe ducts/stacks atthe sampling locations, and distances offlow disturbances, (e.g. elbows, tees, fans, dampers) from the sampling locations (upstream and downstream).
e. Field and laboratory data forms, strip charts and analyses.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section E Page: 5 Facilitv ID: 800074 Revision#: 16 Date: January 14, 2015



## LACITY, DWPHAYNES GENERATING STATION

SECTIONE: ADMINISTRATIVE CONDITIONS

f. Calculations for volumetric flow rates, emission rates, control efficiency, and overall control efficiency. 11. The operator shall, when a source test is required, provide and maintain facilities for sampling and testing. These facilities shall comply with the requirements of SCAQMD Source Test Method I.I and 1.2. [217] 12. Whenever required to submit a written report, notification or other submittal to the Executive Officer, SCAQMD, orthe District, the operator shall mail ordeliverthe material to: Deputy Executive Officer, Engineering and Compliance, SCAQMD, 21865 E. Copley Drive, Diamond Bar, CA 91765-4182. [204]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section F Page: I Facilitv ID: 800074 Revision#: 12 Date: January 14,2015



## LA CITY,DWPHAYNES GENERATING STATION
SECTION F: RECLAIMMONITORINGAND SOURCE TESTING REQUIREMENTS The Facility shall comply with all applicable monitoring and source testing requirements in Regulation XX. These requirements may include but are not limited to the following: 

### I. NOx Monitoring Conditions A. The OperatorofaNOx Major Source, as defined inRule 2012, shall, as applicable: I. 

### Install, maintain, and operate an SCAQMD certified direct ortime-shared monitoring device oran approved alternative monitoring device for each major NOx source to continuously measure the concentration ofNOxemissions and all other applicable variables specified in Rule 2012, Table 2012-1 and Rule 2012, Appendix A, Table 2-Ato determine theNOxemissionsrate from each source. The time-sharing ofCEMS amongNOx sources may be allowedby the Executive Officer in accordance with the requirements for time sharing specified in Appendix A. [2012] 2. Install, maintain, and operate a totalizing fuel meterapproved by the Executive Officer for eachmajor source. [2012] 3. If

### the facility is operating existing CEMS and fuel meters, continue to follow recording andreporting procedures required by SCAQMD Rules and Regulations ineffectpriorto October 15, 1993 until the CEMS is certified pursuant to Rule 2012. [2012] 4. Use valid data collected by an SCAQMD certified orprovisionally certified CEMS inproper operation that meets all the requirements ofAppendix A ofRule 2012, unless final certification oftheCEMS is denied, to determine mass emissions for all purposes, including, butnot limited to, determining: [2012] 

### a. compliance with the annual Allocation; b. excess emissions; c. the amount ofpenalties; and d. fees.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-41 78



## FACILITYPERMITTO OPERATE Section F Page· 2 Facilitv ID: 800074 Revision#: 12 Date: January 14. 2015



## LA CITY,DWPHAYNES GENERATING STATION
SECTION F: RECLAIM MONITORING AND SOURCE TESTING REQUIREMENTS

5. Follow missing dataprocedures as specified inRule 2012 Appendix A whenever valid data is not available orcollected to determine mass emissions for all purposes, including, but not limited to, determining: (2012] 

### a. compliance withthe annual Allocation; b. excess emissions; c. the amountofpenalties; and d. fees.
B. The Operator ofaNOx Large Source, as defined in Rule 2012, shall, as applicable: Not Applicable
C. The Operator ofaNOx Process Unit, as defined in Rule 2012, shall, as applicable: I. 

### Install, maintain, and operate a totalizing fuel meter orany device approved by the Executive Officerto measure quarterly fuel usage orother applicable variables specified in Rule 2012, Table 2012-1, and Rule 2012, Appendix A, Table 4-A. The sharing oftotalizing fuel meters may be allowed by the Executive Officerif the fuel meter serves processunits which have the same emission factor or emission rate. The sharing oftotalizing meter shall not be 

### allowed for process units which are requiredto comply with an annual heat input limit. (2012] II. NOx Source Testing and Tune-up conditions I. 

### The operator shall conduct all requiredNOx source testing in compliance with an SCAQMD-approved source test protocol. (2012]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section F Page: 3 Facilitv ID: 800074 Revision#: 12 Date: January 14. 2015



## LA CITY,DWPHAYNES GENERATINGSTATION
SECTIONF: RECLAIM MONITORING AND SOURCE TESTING REQUIREMENTS

2. The operator shall, as applicable, conduct source tests for every large NOx source no laterthanDecember 31, 1996 and every 3 years thereafter. The sourcetest shall include the determination ofNOxconcentrationand a relative accuracy audit ofthe exhaust stack flow determination (e.g. in-stack flow monitororfuel flow monitorbased F-factor calculation). Such source test results shall be submitted per the schedule described by APEP. Jn lieu ofsubmitting the first source test report, the facility permit holdermay submit the results ofa source test not more than 3 years old which meetsthe requirements when conducted. [2012] 3. All NOx large sources and NOx process units shall be tuned-up in accordance with the schedule specified in Rule 2012, Appendix A, Chapter 5, Table 5-B. [2012]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITY PERMIT TO OPERATE Section G Page: I Facilitv ID: 800074 Revision#: 13 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION SECTION G: RECORDKEEPING AND REPORTING REQUIREMENTS FOR RECLAIM SOURCES The Facility shall comply with all applicable reporting andrecordkeeping requirements in Regulation XX. These requirements may include but are not limited to the following:

I. Recordkeeping Requirements for all RECLAIM Sources I . The operator shall maintainall monitoring datarequired to be measured orreported pursuantto Rule 2011 and Rule 2012, whichever is applicable. All records shall be made available to SCAQMD staffupon request andbe maintained for at least:
a. Three years aftereachAPEP report is submitted to SCAQMD for a facility not subject to Title V, unless a differenttime period is required in Rule 2011 orRule 2012 [2011 & 

### 2012]; or b. Five years aftereach APEP report is submittedto SCAQMD for a facility subject to Title V. [3004(a)(4)(E)] c. Notwithstanding the above, all data gatheredorcomputed for intervals of less than 15 minutes shall onlybe maintained a minimum of48 hours. [2011 & 

### 2012] 2. The operator shall store on site and make available to the Executive Officerupon request: records used to determine emissions, maintenance records, sources test reports, relative accuracy testaudit reports, relative accuracy audit reports and fuel meter calibrationrecords. [2011 & 

### 2012] II. Reporting Requirements for all RECLAIM Sources I. 

### The opearator shall submit a quarterly certification ofemissions including the total facility NOx or SOx emissions, whichever is applicable, for the quarter within 30 days afterthe end ofthe first three quarters and 60 days afterthe end ofthe fourth quarter ofa compliance year. [2004]
NOxReporting Requirements A. The Operatorofa NOx Major Source, as defined in Rule 2012, shall, as applicable:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section G Page: 2 Facilitv ID: 800074 Revision#: 13 Date: January 14. 2015



## LA CITY,DWP HAYNES GENERATING STATION SECTION G: RECORDKEEPINGAND REPORTING REQUIREMENTS FOR RECLAIM SOURCES

1. No laterthan 12 months afterentry into the RECLAIM program orafter the initial operation ofa new major source, whichever is later, install, maintain, and operate a reporting device to electronically report everyday to the SCAQMD central station for each majorNOx source,the total daily mass emissions ofNOx and daily status codes. Such data shall be transmittedby 5:00p.m. ofthe following day. 

### Ifthe facility experiences apower, computer, orother system failure that prevents the submittal ofthe daily report, the Facility Permitholder shall be granted 24

### hours extensionto submit the report. [2012) 2. CalculateNOx emissions pursuant to missing dataprocedures set forth inAppendix A, Chapter2 ofRule 2012 ifthe Facility Permit holderfails to meet the deadline for submittingthe daily report. Notwithstanding the preceding condition, in no more than three non-consecutive occurrences percompliance yearthe reporting deadline extension following a system failure that precludes the Facility Permit holder from timely reporting shall be 96 ratherthan 24

### hours provided that the raw data as obtained by the direct monitoring device is stored at the facility. [2012] 3. Submit anelectronic report within 15 days following the end ofeach month totaling NOX emissions from all majorNOx sources during the month. [2012] 4. Forthose facilities with existing CEMS and fuel meters as ofOctober 15, 1993, continue to follow recording and reporting procedures requiredby SCAQMD Rules and Regulations in effect until the CEMS is certifiedpursuantto Rule 2011 and/or Rule 2012, as applicable. [2012]
B. The Operatorofa NOx Large Source, as defined inRule 2012, shall: Not Applicable
C. The Operator ofaNOx Process Unit, as defined in Rule 2012, shall:

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178



## FACILITYPERMITTO OPERATE Section G Page: 3 Facilitv ID: 800074 Revision#: 13 Date· January 14,2015



## LACITY,DWPHAYNES GENERATING STATION SECTIONG: RECORDKEEPING AND REPORTING REQUIREMENTS FOR RECLAIM SOURCES

1. Electronically reportthe calculated quarterly NOx emissions for eachNOxprocess 

### unit. The Operator shall comply with this requirementwithin 12 months ofthe date ofentry to the RECLAIM Program. [2012]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTO OPERATE Section H Page: I Facility ID: 800074 Revision#: 30 Date: January 14, 2015



## LA CITY, DWPHAYNES GENERATING STATION SECTION H: PERMITTO CONSTRUCTAND TEMPORARY PERMITTO OPERATE



# NONE

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE LA CITY,DWPHAYNES GENERATING STATION

SECTION I: PLANS AND SCHEDULES Section I Page· I Facilitv JD· 800074 Revision#: 10 Date: January 14, 2015

This section lists all plans approved by AQMD for the purposes of meeting the requirements of applicable AQMDrules.



## NONE

NOTE: This section does not list compliance schedules pursuant to the requirements of Regulation XXX

- Title V Permits; Rule 3004(a)(IO)(C). For equipment subject to a variance, order for abatement, or alternative operating condition granted pursuant to Rule 518.2, equipment specific conditions are added to the equipment in Section Dor Hofthe permit.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section J Page: I Facility ID: 800074 Revision#: 7 Date: January 14. 2015



## LA CITY,DWPBAYNESGENERATING STATION SECTIONJ: AIRTOXICS



### NOT APPLICABLE

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section K Page: I Facility ID: 800074 Revision#: 8 Date· January 14. 2015



## LACITY,DWPHAYNES GENERATING STATION SECTION K: TITLE V Administration GENERALPROVISIONS 1. This pennit may be revised, revoked, reopened and reissued, or tenninated for cause, or for failure to comply with regulatory requirements, pennit tenns, or conditions. [3004(a)(7)(C)] 2. This pennit does not convey any property rights ofany sort or any exclusive privilege. [3004(a)(7)(E)] PermitRenewal and Expiration 3. (A) Except for solid waste mcmeration facilities subject to standards under section 129(e) ofthe Clean Air Act, this pennit shall expire five years from the date that this Title V pennit is issued. The operator's right to operate under this pennit tenninates at midnight on this date, unless the facility is protected by an application shield in accordance with Rule 3002(b), due to the filing ofa timely and complete application for a Title V pennitrenewal, consistent with Rule 3003. [3004(a)(2), 3004(t)] (B) A Title V pennit for a solid waste incineration facility combusting municipal waste subject to standards under Section 129( e) ofthe Clean Air Act shall expire 12 years from the date ofissuance unless such pennit has been renewed pursuant to this regulation. These pennits shall be reviewed by the Executive Officer at least every five years from the date ofissuance. [3004(t)(2)] 4. To renewthis pennit, theoperator shall submitto theExecutive Officeran application for renewal atleast 

### J80 days, but not more than 545 days, prior to the expiration date ofthis pennit. [3003(a)(6)] DutytoProvideInformation 5. The applicant for, or holder of, a Title V pennit shall furnish, pursuant to Rule 3002(d) and ( e), timely infonnation and records to the Executive Officer or designee within a reasonable time as specified in writing by the Executive Officer or designee. [3004(a)(7)(F)] PaymentofFees 6. Theoperator shallpayall required fees specified in Regulation Ill

- Fees. [3004(a)(7)(G)]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section K Page: 2 Fac:ilitv ID: 800074 Revision#' 8 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION SECTION K: TITLE V Administration Reopening for Cause 7. The Executive Officer will reopen and revise this permit if any of the following circumstances occur: (A) Additional regulatory requirements become applicable with a remaining permit term ofthree or more years. Reopening is not required ifthe effective date ofthe requirement is later than the expiration date ofthis permit, unless the permit or any ofits terms and conditions has been extended pursuant to paragraph (f)(4) 

### of Rule 3004. (B) 

### The Executive Officer orEPA Administrator determines that this permit contains a material mistake or that inaccurate statements were made in establishing the emissions standards or otherterms orconditions ofthis permit. (C) 

### The Executive Officer or EPA Administrator determines that the permit must be revised or revoked to assure compliance with the applicable requirements. [3005(g)(l)] COMPLIANCEPROVISIONS 8. The operator. shall comply with all regulatory requirements, and all permit terms and conditions, except: (A) As provided for bythe emergency provisions ofcondition no. 17 or condition no. 18, or (B) 

### As provided by an alternative operating condition granted pursuant to a federally approved (SIP-approved) Rule 518.2. Any non-compliance with any federally enforceable permitcondition constitutes a violation ofthe Federal Clean Air Act and is grounds for enforcement action; for permit termination, revocation and reissuance, or revision; or denial ofa permit renewal application. Non-compliance may also be grounds for civil or criminal penalties under the California State Health and Safety Code. (3004(a)(7)(A)]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section K Page· 3 Facility ID: 800074 Revision #: 8 Date: January 14, 2015



## LACITY,DWPHAYNES GENERATING STATION SECTION K: TITLE V Administration 9. The operator shall allow the Executive Officer or authorized representative, upon presentation ofappropriatecredentialsto: (A) Enter the operator's premises where emission-related activities are conducted, or records are keptunderthe conditions ofthis permit; (B) Have access to and copy, atreasonable times, any records that mustbe keptunder theconditions ofthe permit; (C) Inspect at reasonable times, any facilities, equipment (including monitoring and air pollution control equipment), practices, or operations regulated or required underthe permit; and (D) Sample or monitor at reasonable times, substances or parameters for the purpose of assuring compliance with the facility permit or regulatory requirements. [3004(a)(l

### O)(B)]
10. All terms and conditions in this permit, including any provisions designed to limit a facility's potential to emit, are enforceable by the EPA Administrator and citizens under the federal Clean Air Act, unless the term or condition is designated as not federally enforceable. Each day during any portion of which a violation occurs is a separate offense. [3004(g)) 11. A challenge to any permit condition or requirement raised by EPA, the operator, or any other person, shall not invalidate or otherwise affect the remaining portions of this permit. [3007(b)) 12. The filing of any application for a permit revision, revocation, or termination, or a notification ofplanned changes or anticipated non-compliance does not stay any permit condition. [3004(a)(7)(D)] 13. It shall not be a defense for a person in an enforcement action, including those listed in Rule 3002(c)(2), thatitwould havebeen necessary tohalt or reduce thepermitted activity in orderto maintain compliance with the conditions ofthis permit, exceptas provided for in "Emergency Provisions" ofthis section. [3004(a)(7)(H)]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section K Page: 4 Facilitv ID 800074 Revision#: 8 Date: January 14. 2015



## LA CITY, DWPHAYNES GENERATING STATION SECTION K: TITLE V Administration 14. The operator shall not build, erect, install, or use any equipment, the use of which, without resulting in a reduction in the total release ofair contaminants to atmosphere, reduces or conceals an emission which would otherwise constitute a violation ofChapter 3 (commencing with Section 41700) ofPart 4, ofDivision 26 ofthe California Health and Safety Code or ofAQMD rules. This rule shall not apply to cases in which the only violation involved 

### is ofSection 41700 ofthe California Health and Safety Code, or Rule 402 ofAQMD Rules. (408] 15. Nothing in thispermitor in any permit shield can alter oraffect: (A) Under Section 303 ofthefederal Clean Air Act, the provisions for emergency orders; (B) The liability ofthe operator for anyviolation ofapplicablerequirements priorto or atthetime ofpermit issuance; (C) The applicable requirements ofthe Acid Rain Program, Regulation XXXI; (D) The ability ofEPAto obtain information from theoperatorpursuantto Section 114 ofthe federal Clean Air Act; (E) The applicability of state or local requirements that are not "applicable requirements'', as defined in Rule 3000, at the time ofpermit issuance but which do apply to the facility, such as toxics requirements unique to the State; and (F) The applicability of regulatory requirements with compliance dates after the permit issuance date. [3004(c)(3)] 16. For any portable equipment that requires an AQMD or state permit or registration, excluding a) portable engines, b) military tactical support equipment and c) AQMDpermitted portable equipment that are not a major source, are not located at the facility for more than 12 consecutive months after commencing operation, and whose operation does not conflict with the terms or conditions of this Title V permit: 1) the facility operator shall keep a copy ofthe AQMD or state permit orregistration; 2) the equipment operator shall comply with the conditions on the permit or registration and all other regulatory requirements; and 3) the facility operator shall treat the permit or registration as a part of its Title V permit, subject to recordkeeping, reporting and certification requirements. [3004(a)(l)]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-4178



## FACILITYPERMITTOOPERATE Section K Page: 5 Facility ID: 800074 Revision#: 8 Date: January 14, 2015



## LA CITY,DWPHA YNES GENERATING STATION SECTION K: TITLE V Administration EMERGENCYPROVISIONS 17. An 

### emergency' constitutes an affirmative defense to an action broughtfor noncompliance with atechnology-based emission limit only if: (A) Properly signed, contemporaneous operating records or other credible evidence demonstratethat: (1) An 

### emergency occurred and the operator can identify the cause(s) ofthe emergency; (2) The facility was 

### operated properly (i.e. operated and maintained in accordance with the manufacturer's specifications, and in compliance with all regulatory requirements or a compliance plan), before the emergency occurred; (3) The operatortook all reasonable steps to minimize levels ofemissions that exceeded emissions standard, or otherrequirements inthe permit; and, (4) The operator submitted a written notice ofthe emergency to the AQMD within two working days ofthe time when the emissions limitations were exceeded due to the emergency. The notice shall contain a description of the emergency, any steps taken to mitigate emissions, and corrective actions taken; and 

### (B) The operator complies with the breakdown provisions ofRule 430

- Breakdown Provisions, or subdivision (i) of Rule 2004

- Requirements, whichever is applicable. [3002(g), 430, 2004(i)] 18. The operator is excused from complying with any regulatory requirement that is suspended by the Executive Officer during a state of emergency or state of war emergency, in accordance with Rule 118

-Emergencies. [118]
1 "Emergency" means any situation arising from sudden and reasonably unforeseeable events beyond the control of the operator, including acts of God, which: (A) requires immediate corrective action to restore normal operation; and (B) causes the facility to exceed atechnologybased emission limitation underthe permit, due to unavoidable increases in emissions attributable to the emergency; and (C) is not caused by improperly designed equipment, lack ofpreventative maintenance, careless or improperoperation, oroperatorerror.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section K Page: 6 Facilitv ID: 800074 Revision#: 8 Date: January 14, 2015



## LA CITY, DWPHAYNES GENERATING STATION SECTION K: TITLE V Administration RECORDKEEPINGPROVISIONS 19. In addition to any other recordkeeping requirements specified elsewhere in this permit, the operator shall keep records ofrequiredmonitoring information, where applicable, that include: (A) The date, placeas defined in the Title V permit, andtime ofsampling or measurements; (B) The date(s) analyses wereperformed; (C) Tlie company orentitythatperformed the analyses; (D) The analyticaltechniques ormethods used; (E) Theresults ofsuch analyses; and (F) The operating conditions as existingatthe time ofsampling ormeasurement. [3004(a)(4)(B)]

20. The operator shall maintain records pursuant to Rule I09 and any applicable material safety data sheet (MSDS) for any equipment claimed to be exempt from a written permit byRule219 based onthe information inthose records. [2!9(t)] 21. The operator shall keep all records of monitoring data required by this permit or by regulatory requirements for a period ofat leastfive years from the date ofthe monitoring sample, measurement, report, orapplication. [3004(a)(4)(E)] REPORTINGPROVISIONS 22. The operator shall comply with the following requirements for prompt reporting of deviations: (A) Breakdowns shallbereported as requiredbyRule 430

- BreakdownProvisions or subdivision (i) ofRule 2004

- Requirements, whicheveris applicable.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMITTOOPERATE Section K Page: 7 Facilitv ID: 800074 Revision#· 8 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION SECTION K: TITLE V Administration (B) Other deviations from permit or applicable rule emission limitations, equipment operating conditions, orwork practice standards, determined by observation or by any monitoring or testing required by the permit or applicable rules that result in emissions greater than those allowed by the permit or applicable rules shall be reported within 72 hours (unless a shorter reporting period is specified in an applicable State or Federal Regulation) of discovery of the deviation by contacting AQMD enforcement personnel assigned to this facility or otherwise calling (800) CUT-SMOG. (C) A written report ofsuch deviations reported pursuant to (B), 

### and any corrective actions or preventative measures taken, shall be submitted to AQMD, m an AQMD approved format, within 14 days ofdiscovery ofthe deviation. (D) All other deviations shall be reported with the monitoring report required by conditionno. 23. [3004(a)(5)]
23. Unless more frequent reporting of monitoring results are specified in other permit conditions or in regulatory requirements, the operator shall submitreports ofany required monitoring to the AQMD at least twice per year. The report shall include a) a statement whether all monitoring required by the permit was conducted; and b) identification ofall instances ofdeviations from permit orregulatory requirements. A report for the first six calendar months ofthe year is due by August 31 and a report for the last six calendar months ofthe year is dueby February 28. [3004(a)(4)(F)] 24. The operator shall submit to the Executive Officer and to the Environmental Protection Agency (EPA), an annual compliance certification. For RECLAIM facilities, the certification is due when the Annual PermitEmissions Program (APEP) report is due and shall cover the same reporting period. For other facilities, the certification is due on March I for the previous calendar year. The certification need not include the period preceding the date the initial Title V permit was issued. Each compliance certification shall include: (A) Identification ofeach permitterm orcondition that is the basis ofthe certification;

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITY PERMIT TO OPERATE Section K Page: 8 Facilitv ID: 800074 Revision#: 8 Date: January 14, 2015



## LA CITY,DWPHAYNES GENERATING STATION SECTION

## K: TITLE V Administration (B) Thecompliance statusduringthe reporting period; (C) Whethercompliancewas continuous or intermittent; (D) The method(s) used to determinecomplianceoverthe reportingperiod and currently, and (E) Any otherfacts specifically required bythe Executive Officerto determine compliance. TheEPAcopy ofthe certification shall be sent to: Directorofthe AirDivision Attn: Air-3 USEPA,Region IX75 Hawthorne St. San Francisco, CA94105 [3004(a)(I

### O)(E)] 25. All records, reports, and documents required to be submitted by a Title V operator to AQMD or EPA shall contain a certification ofaccuracy consistent with Rule 3003(c)(7) by a responsible official (as defined in Rule 3000). [3004(a)(12)] PERIODIC MONITORING 26. All periodic monitoring required by this permit pursuant to Rule 3004(a)(4)(c) is based on the requirements and justifications in the AQMD document "Periodic Monitoring Guidelines for Title V Facilities" or in case-by-case determinations documented in the TitleVapplicationfile. [3004(a)(4)]- ... ------------------------------- 

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178 Section K Page: 9 Facility ID: 800074 Revision #: 8 Date: January 14. 2015 

## FACILITYPERMIT TOOPERATE LACITY, DWPHAYNES GENERATING STATION
SECTION K: TITLE V Administration FACILITYRULES Thisfacility issubject to thefollowing rules andregulations

With the exception of Rule 402, 473, 477, 1118 and Rules 1401 through 1420, the following rules that are designated as non-federally enforceable are pending EPA approval as part of the state implementation plan. Upon the effective date of that approval, the approved rule(s) will become federally enforceable, and any earlier versions of those rules will no longer be federally enforceable.
RULE SOURCE Adopted/Amended Date FEDERAL Enforceability RULE 1110.2 2-1-2008 Federally enforceable RULE 1113 11-8-1996 Federally enforceable RULE 1113 7-13-2007 Federally enforceable RULE 1140 2-1-1980 Federally enforceable RULE 1140 8-2-1985 Non federally enforceable RULE 1171 11-7-2003 Federally enforceable RULE 1171 2-1-2008 Federally enforceable RULE 118 12-7-1995 Non federally enforceable RULE 1303(a)(I)-BACT 12-6-2002 Non federally enforceable RULE 1303(a)(l)-BACT 5-10-1996 Federally enforceable RULE 1303(b)(l)-Modeling 12-6-2002 Non federally enforceable RULE 1303(b)(l)-Modeling 5-10-1996 Federally enforceable RULE 1303(b)(2)-0ffset 12-6-2002 Non federally enforceable RULE 1303(b)(2)-0ffset 5-10-1996 Federally enforceable RULE 1304(a)-Modeling and 6-14-1996 Federally enforceable Offset Exemption RULE 1304(c)-Offset 6-14-1996 Federally enforceable Exemption RULE 1411 3-1-1991 Non federally enforceable RULE 1470 5-4-2012 Non federally enforceable RULE 1470 6-1-2007 Non federally enforceable RULE 1703

- PSD Analysis 10-7-1988 Federally enforceable

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-41 78 Section K Facilitv ID: Revision#: Page: 10 800074 8 Date: January 14, 2015 

## FACILITYPERMITTOOPERATE LA CITY, DWP HAYNES GENERATING STATION
SECTIONK: TITLE V Administration RULE SOURCE Adopted/Amended Date FEDERALEnforceability RULE2005 4-20-2001 Federally enforceable RULE2005 4-9-1999 Federally enforceable RULE2005 6-3-2011 Federally enforceable RULE2009 5-11-2001 Non federally enforceable RULE2012 12-5-2003 Federally enforceable RULE2012 5-11-2001 Federally enforceable RULE 2012 5-6-2005 Federally enforceable RULE204 10-8-1993 Federally enforceable RULE 217 1-5-1990 Federally enforceable RULE 218 5-14-1999 Federally enforceable RULE 218 8-7-198l Federally enforceable RULE 219 9-4-1981 Federally enforceable RULE 3002 11-14-1997 Federally enforceable RULE 3003 11-14-1997 Federally enforceable RULE 3004(a)(4)-Periodic 12-12-1997 Federally enforceable Monitoring RULE3005 11-14-1997 Federally enforceable RULE 3007 10-8-1993 Federally enforceable RULE304 l-14-1982 Non federally enforceable RULE 401 11-9-2001 Non federally enforceable RULE 401 3-2-1984 Federally enforceable RULE402 5-7-1976 Non federally enforceable RULE404 2-7-1986 Federally enforceable RULE405 2-7-1986 Federally enforceable RULE407 4-2-1982 Federally enforceable RULE408 5-7-1976 Federally enforceable RULE409 8-7-1981 Federally enforceable RULE430 7-12-1996 Non federally enforceable RULE 431.l 11-17-1995 Non federally enforceable RULE 431.2 5-4-1990 Federally enforceable RULE 431.2 9-15-2000 Non federally enforceable RULE463 3-11-1994 Federally enforceable RULE464 12-7-1990 Federally enforceable

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Section K Page: 11 Facilitv lD: 800074 Revision#: 8 Date: January 14,2015



## LACITY,DWP HAYNES GENERATING STATION
SECTION K: TITLE V Administration RULE SOURCE Adopted/Amended Date FEDERAL Enforceability RULE475 10-8-1976 Federally enforceable RULE 475 8-7-1978 Non federally enforceable RULE 701 6-13-1997 Federally enforceable CAPRCCEQA 11-23-1970 Non federally enforceable 40CFR 60 Subpart Da 10-4-1991 Federally enforceable 40CFR 60 Subpart GG 3-6-1981 Federally enforceable 40CFR 60 Subpart III! 7-11-2006 Federally enforceable 40CFR 60 Subpart KKKK 7-6-2006 Federally enforceable 40CFR 63 Subpart ZZZZ 1-30-2013 Federally enforceable 40CFR 68

- Accidental 5-24-1996 Federally enforceable Release Prevention 40CFR 72

- Acid Rain 11-24-1997 Federally enforceable Provisions 40CFR73 Subpart B 1-11-1993 Federally enforceable 40CFR 82 Subpart B 7-14-1992 Federally enforceable 40CFR Part 51, Appendix S 10-20-2010 Federally enforceable

### South Coast Air Quality Management District 2

### t865 Copley Drive, Diamond Bar, CA 91 765-4

### t78



## FACILITYPERMITTOOPERATE Appendix A Page: I Facilitv JD· 800074 Revision#: 9 Date: January 14. 2015



## LA CITY, DWPBAYNES GENERATING STATION

APPENDIX A: NOX AND SOX EMITTING EQUIPMENT EXEMPT FROM WRITTEN PERMITPURSUANT TO RULE 219

1. VACUUM, GASOLINE 

### 2. BACKPACKAIRBLOWER, GASOLINE 

### 3. CHAIN SAW, GASOLINE 

### 4. CONCRETE SAW, GASOLINE 

### 5. AIRCOMPRESSOR, GASOLINE 

### 6. CONCRETE MIXERS, GASOLINE 

### 7. WELDER, GASOLINE 

### 8. WATERBLASTER, GASOLINE 

### 9. IC ENGINES

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91 765-41 78 Appendix B Page: I Facilitv ID: 800074 Revision#: 1 Date: January 14. 2015 

## FACILITYPERMITTOOPERATE LACITY.DWPHAYNES GENERATING STATION
APPENDIX B: RULE EMISSIONLIMITS [RULE 1113 11-08-1996) 

### (I) Except as provided in paragraphs (c)(2), (c)(3), and (c)(4) of Rule 1113, the operator shall not supply, sell, offer for sale, apply, or solicit the application of, any architectural coating which, at the time ofsale or manufacture, contains more than 

### 250 grams ofVOeperliter ofcoating (2.08 pounds per gallon), less water, Jess exempt compounds, and less any colorant added to tint bases, or manufacture, blend, or repackage such acoatingforuse withinthe District. (2) Except as provided in paragraphs (c)(3) and (c)(4) of Rule 1113, the operator shall not supply, sell, offer for sale, apply, solicit the application of, manufacture, blend, or repackage, for use within the District, any architectural coating listed in the Table ofStandards which contains voe (excluding any colorant added to 

### tintbases) in excess of the corresponding voe limit specified in the table, after the effective date specified. TABLE OF STANDARDS VOCLIMITS Grams ofVOCPerLiterofCoating, LessWaterAnd Less ExemptCompounds COATING Limit* Effective Effective Effective Effective Effective Effective Dateof 1/1/1998 111/1999 7/1/2001 1/1/2005 7/112008 Adootion Bond Breai<ers 350 Clear WoodFinishes

Varnish 350 Sanding Sealers 350 Lacquer 680 550 275 Concrete-Curing Compounds 350 Dry-Fog Coatings 400 Fire-proofingExterior 350 450 350 Coatmgs Fire-RetardantCoatings

Clear 650 Pigmented 350 Flats 250 100 

## so Graphic Arts (Sign) Coatings 500

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTO OPERATE LACITY.DWPHAYNES GENERATING STATION

IndustrialMaintenance Primers and Topcoats

Alkyds Catalyzed Epoxy BituminousCoatings Materials

Inorganic**Po~ers** Vinyl Chlori e Polymers ChlorinatedRubber Acrylic Polymers UrethanePolymers Silicones Unique Vehicles Japans/Faux Finishing Coatings Magnesite CementCoatings Mastic Coatings Metallic Pigmented Coatings Multi-Color Coatings APPENDIX B: RULE EMISSION LIMITS !RULE 1113 11-08-1996)
420 420 420 420 420 420 420 420 420 420 350 700 350 600 450 300 500 420 250 Appendix B Page: 2 Facility ID 800074 Revision#: 7 Date: January 14.2015

Pigmented Lacquer 680 550 275 Pre-TreatmentWash Primers 780 Primers, Sealers, and 350 Undercoaters Quick-Dry Enamels 400 RoofCoatings 300 Shellac

Clear 730 Pigmented 550 Stains 350 SwimmingPool Coatings

Repair 650 Other 340 Traffic Coatings 250 150 Waterproofmg Sealers 400 Wood Preservatives

Below-Ground 350 Other 350 

## * The specified hmits remam in effect unless revised limits are listed in subsequent columns m the Table ofStandards 

### TABLE OFSTANDARDS (cont.) 

### VOCLIMITS Grams ofVOC PerLiterofMaterial
COATING Low-Solids Coating Limit 120

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMIT TOOPERATE LA CITY.DWPHA YNES GENERATING STATION
APPENDIXB: RULE EMISSION LIMITS [RULE 1113 07-13-20071 

### (1) Except as provided in paragraphs (c)(2), (c)(3), (c)(4), and specified coatings averaged under ( c)(6), no person shall supply, sell, offer for sale, manufacture, blend, or repackage any architectural coating for use in the District which, at the time ofsale or manufacture, contains more than 250 grams of

## voe per liter ofcoating (2.08 pounds per gallon), less water, less exempt compounds, and less any colorant added to tint bases, and no person shall apply or solicit the application ofany architectural coating within the District that exceeds 250 grams ofVOC per liter ofcoating as calculated in this paragraph. (2) Except as provided in paragraphs (c)(3), (c)(4), and designated coatings averaged under ( c)(6), no person shall supply, sell, offer for sale, manufacture, blend, or repackage, for use within the District, any architectural coating listed in the Table of Standards which contains VOC (excluding any colorant added to tint bases) in excess ofthe corresponding 

## voe limit specified in the table, after the effective date specified, and no person shall apply or solicit the application of any architectural coating within the District that exceeds the VOC limit as specified in this paragraph. No person shall apply or solicit the application within the District of any industrial maintenance coatings, except anti-graffiti coatings, for residential use or for use in areas such as office space and meeting rooms ofindustrial, commercial or institutional facilities not exposed to such extreme environmental conditions described in the definition of industrial maintenance coatings; or ofany rust-preventative coating for industrial use, unless such a rust preventative coating complies with the Industrial Maintenance CoatingVOC limit specified in the Table ofStandards. Appendix B Page: 3 Facility ID: 800074 Revision#: 7 Date: January 14, 2015

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTO OPERATE LACITY.DWPHAYNES GENERATING STATION APPENDIX B: RULE EMISSION LIMITS [RULE 1113 07-13-2007] TABLE OFSTANDARDS VOCLIMITS GramsofVOCPerLiterofCoating, LessWaterand Less ExemptCompounds 

### '' COA'ltNGCA:;TEGOltY

..**~g** '1Zui'rent ye.. .**~;;c >~!Tecllv~l)(lte** 

- :" ;_
- -, J)ilnjt• >Lbnit .··**i!:I>~. ~iJJD,t** 

---k'·'iX<'.**~** -

### :!IJP~**7~\l!Ji** Bond Breakers 350 ClearWood Finishes 350 275 Varnish 350 275 Sanding Sealers 350 275 Lacquer 680 550 275 ClearBrushing Lacquer 680 275 Concrete-CuringCompounds 3SO Concrete-CuringCompounds 3SO ForRoadways and Bridges** Drv-FogCoatings 400 Fire-Proofing ExteriorCoatings 4SO 350 Fire-RetardantCoatings*** Clear 6SO Pigmented 3SO Flats 2SO 100 FloorCoatings 420 100 50 Graphic Arts !Sion\ Coatinos SOD Industrial Maintenance (IM) 420 2SO 100 Coatings High TemperatureIM 420 Coatings Zinc-Rich IMPrimers 420 340 100 Japans/Faux FinishingCoatings 700 350 Magnesite Cement Coatings 600 450 Mastic Coatings 300 MetallicPigmented Coatings SOD Multi-ColorCoatings 420 2SO Nonflat Coatings 250 ISO 50 Appendix B Page: 4 Facilitv ID· 800074 Revision #: 7 Date: January 14,2015

### ~Fr' 

### 'T**7/~,**

"c • k:**i~**

100

ISO



### so

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMIT TO OPERATE LA CITY.DWPHAYNES GENERATING STATION
APPENDIXB: RULE EMISSIONLIMITS [RULE 1113 07-13-2007)

NonflatHigh Gloss PigmentedLacquer Pre-TreatmentWash Primers Primers, Sealers, and Undercoaters Quick-DryEnamels Quick-DryPrimers, Sealers,

and Undercoaters Recycled Coatings RoofCoatings RoofCoatings, Aluminum RoofPrimers,Bituminous Rust PreventativeCoatin s Shellac Clear

Stains, Interior SwimmingPoolCoatings Repair Other Traffic Coatings Waterproofing

Concrete/Masonry Sealers WoodPreservatives Below-Ground Other 250 680 780 350
400 350

300 500 350 420 730 550 350 350 250
650 340 250 400 400

350 350 550

150 150
420 200
250 200
250 250
350 400

250

340

250 275

50 100 100 150 100

100

250

100 100 Appendix B Page: 5 Facility ID: 800074 Revision#: 7 Date: January 14, 2015

50

50

100 100

100

• The specified limitsremain in effectunlessrevised limits are listed in subsequentcolumns in theTableof Standards. 

## ** Doesnotinclude compoundsused for curbs and gutters, sidewalks, islands, driveways andother miscellaneous concrete areas. 

## *** TheFire-Retardant Coating category will beeliminated onJanuary 1, 2007 and subsumedbythe coating category for which they are formulated.

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTOOPERATE LACITY.DWPHAYNES GENERATINGSTATION
APPENDIX B: RULE EMISSION LIMITS [RULE 1113 07-13-2007) 

### TABLE OF STANDARDS (cont.) 

### VOCLIMITS GramsofVOCPerLiterofMaterial 

# I COATING

Low-Solids Coating Limit 120 Appendix B Page: 6 Facilitv ID: 800074 Revision#: 7 Date: January 14, 2015

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTOOPERATE LACITY.DWPHAYNES GENERATINGSTATION
APPENDIXB: RULE EMISSION LIMITS [RULE 1140 02-01-1980] (1) The operator shall not, if he complies with an applicable performance standard in section (b)(4) ofRule 1140, discharge into the atmosphere from any abrasive blasting any air contaminant for a period or periods aggregating more thanthree minutes in any one hourwhich is: (A) As dark or darker in shade as that designated as No. 2 on the Ringelmann Chart, as published by the United States Bureau of Mines, or (B) Ofsuch opacity as to obscure an observer's viewto a degree equal to orgreaterthan does smoke described in (1)(A). (2) The operator shall not, ifheis not complying with an applicable performance standard in section (b)(4) ofRule 1140, discharge into the atmosphere from any abrasive blasting any air contaminant for a period or periods aggregating more thanthree minutes in any one hourwhich is: (A) As dark or darker in shade as that designated as No. 1 on the Ringelmann Chart, as published by the United States Bureau of Mines, or (B) Ofsuch opacity as to obscure an observer's viewto a degree equal to orgreaterthan does smokedescribed in (2)(A). Appendix B Page: 7 Facilitv ID: &00074 Revision#: 7 Date: January 14, 2015

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTO OPERATE LA CITY. DWPHAYNES GENERATING STATION
APPENDIXB: RULE EMISSIONLIMITS [RULE 1140 08-02-1985] (I) The operator shall not, if he complies with an applicable performance standard in section (b)(4) ofRule 1140, discharge into the atmosphere from any abrasive blasting any air contaminant for a period or periods aggregating more than threeminutes in any one hourwhich is: (A) As dark or darker in shade as that designated as No. 2 on the Ringelmann Chart, as published by the United States Bureau of Mines, or (B) Ofsuch opacity as to obscure an observer's view to a degree equal to orgreaterthan does smokedescribed in (l)(A). (2) The operator shall not, ifhe is notcomplying with an applicable performance standard in section (b)(4) ofRule 1140, discharge into the atmosphere from any abrasive blasting any air contaminant for a period orperiods aggregating more than three minutes in any one hour which is: (A) As dark or darker in shade as that designated as No. 1 on the Ringelmann Chart, as published by the United States Bureau of Mines, or (B) Ofsuch opacity as to obscure an observer's view to a degree equal to orgreaterthan does smokedescribed in (2)(A). Appendix B Page: 8 Facility ID: 800074 Revision#: 7 Date: January 14, 2015

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMIT TO OPERATE Appendix 8 Page: 9 Facilitv ID: 800074 Revision#: 7 Date: January 14, 2015


## LA CITY. DWPHAYNESGENERATING STATION
APPENDIXB: RULE EMISSION LIMITS [RULE 117111-07-2003) (1) SolventRequirements A person shall not use a solventto perform solventcleaning operations unless the solvent complies 

### with the applicable requirements setforth below:
CURRENT LIMITS SOL VENT CLEANINGACTIVITY 

# voe g/l (lb/gal) (A) ProductCleaningDuringManufacturing Process OrSurface Preparation ForCoating, Adhesive, OrInkApplication (i) General 25 (0.21) (ii) Electrical Apparatus Components & Electronic 500 Components (4.2) (iii) Medical Devices & Pharmaceuticals 800 (6.7) (B) RepairandMaintenanceCleaning (i) General 25 (0.21) (ii) Electrical Apparatus Components & 900 Electronic Components (7.5)

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTOOPERATE Appendix B Page: 10 Facility ID: 800074 Revision#· 7 Date: January 14, 2015


## LACITY.DWPHAYNES GENERATING STATION
APPENDIX B: RULE EMISSION LIMITS [RULE 117111-07-2003)



### SOLVENT CLEANINGACTNITY
(iii) MedicalDevices & 

### Pharmaceuticals (A) Tools, Equipment, & 

### Machinery (B) 

### General Work Surfaces (C) Cleaning ofCoatings orAdhesives Application Equipment (D) 

### Cleaning ofInk Application Equipment (i) General (ii) Flexographic Printing (iii) Gravure Printing (A) Publication (B) 

### Packaging (iv) Lithographic orLetterPress Printing CURRENT LIMITS



# voe

g/l (lb/gal)

800 (6.7) 600 (5.0) 550 (4.6)

25 (0.21)

25 (0.21)

750 (6.3)

25 (0.21)

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTOOPERATE Appendix B Page: 11 Facility ID: 800074 Revision#: 7 Date: January 14,2015


## LACITY.DWPHAYNES GENERATING STATION

(v) APPENDIX B: RULE EMISSIONLIMITS [RULE 117111-07-2003)

SOL VENT CLEANINGACTMTY
(A) RollerWash

- Step 1 (B) RollerWash-Step2, BlanketWash, & On-Press Components (C) Removable Press Components
Screen Printing (vi) Ultraviolet fuk/ElectronBeamfuk Application Equipment (except screen printing) (vii) SpecialtyFlexographic Printing (E) Cleaning ofPolyesterResin ApplicationEquipment CURRENT LIMITS



# voe

g/l (lb/gal)

600 (5.0) 800 (6.7)

25 (0.21)

750 (6.3) 800 (6.7) 600 (5.0)

25 (0.21)

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-41 78


## FACILITYPERMITTOOPERATE Appendix B Page: 12 Facility ID: 800074 Revision#: 7 Date: January 14, 2015


## LACITY.DWPHAYNES GENERATING STATION
APPENDIX B: RULE EMISSIONLIMITS [RULE 1171 02-01-2008] 

### (1) SolventRequirements A person shall notuse a solventto perform solventcleaningoperations unless the solventcomplies with theapplicablerequirements setforth below:

. 

### CURRENT EFFECTlVE EFFECTIVE

LIMITS* 11112008* 11112009 

# voe voe voe SOLVENT CLEANINGACTIVITY g/I g/I g/I

. 

### (lb/eal) (lb/eal).

. 

### (lb/eal) (A) ProductCleaningDuring ManufacturingProcess Or Surface Preparation ForCoating, Adhesive, OrInk Application (i) General 25 (0.21) (ii) Electrical Apparatus 100 Components & Electronic (0.83) Components (iii) Medical Devices & 800 Pharmaceuticals 

### (6.7) (B) RepairandMaintenance Cleaning (i) General 25 (0.21) (ii) Electrical Apparatus 100 Components & Electronic (0.83) Components

### South Coast Air Quality Management District 21865 Copley Drive. Diamond Bar, CA 91765-4178


## FACILITYPERMITTOOPERATE Appendix B Page: 13 Facilitv ID: 800074 Revision #· 7 Date: January 14, 2015


## LACITY.DWPHAYNES GENERATING STATION
APPENDIX B: RULE EMISSIONLIMITS [RULE 1171 02-01-2008) 

### CURRENT EFFECTIVE

LIMITS* 1/112008* 

# voe voe SOLVENT CLEANINGACTIVITY g/I g/I 

### (cont.) (lb/gal) (lb/gal) (iii) Medical Devices & Pharmaceuticals (A) Tools,Equipment, & 800 Machinery (6.7) (B) General Work Surfaces 600 (5.0) (C) Cleaning ofCoatings orAdhesives 25 Application Equipment (0.21) (D) Cleaning ofInk Application Equipment (i) General 25 (0.21) (ii) Flexographic Printing 25 (0.21) (iii) Gravure Printing (A) Publication 100 (0.83) (B) Packaging 25 (0.21) (iv) Lithographic (Offset) orLetterPress Printing (A) RollerWash, BlanketWash, & On-Press Components (I) Newsprint 100 (0.83) 

### EFFECTIVE 1/112009



# voe

g/I (lb/gal)

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-41 78


## FACILITYPERMITTOOPERATE Appendix B Page: 14 Facility ID: 800074 Revision#: 7 Date: January 14,2015


## LACITY.DWP HAYNES GENERATING STATION
APPENDIXB: RULE EMISSIONLIMITS [RULE 1171 02-01-20081 

### CURRENT EFFECTIVE

LIMITS* 1/112008* 

# voe voe SOLVENT CLEANINGACTIVITY g/I g/I (cont.) (lb/gal) (lb/gal) (II) OtherSubstrates 500 100 (4.2) (0.83) (B) Removable Press Components 25 (021) (v) Screen Printing 500 100 (42) (0.83) (vi) Ultravioletfuk/Electron Beam Ink 650 650 ApplicationEquipment(except (5.4) (5.4) screenprinting) (vii)SpecialtyFlexographicPrinting 100 (083) (E) Cleaning ofPolyesterResin Application 25 Equipment (0.21) 

### EFFECTIVE 1/112009



# voe

g/I (lb/gal)

100 (0.83)



## *The specified hm1ts remam m effectunless revised hm1ts are hsted m subsequent columns.

### South Coast Air Quality Management District Z1865 Copley Drive. Diamond Bar, CA 91765-4178


## FACILITYPERMIT TOOPERATE Appendix B Page: 15 Facility ID: 800074 Revision#: 7 Date: January 14. 2015


## LACITY.DWPHAYNES GENERATING STATION
APPENDIXB: RULE EMISSION LIMITS [RULE 404 02-07-1986) 

### The operator shall not discharge intothe atmosphere from this equipment, particulate matterin excess ofthe concentration at standard conditions, shown in Table 404(a). Where the volume discharged is between figures listed in the Table, the exact concentration permitted to be discharged shall be determined by linear interpolation. Forthe purposes ofthis rule, emissions shall beaveraged over one complete cycle of operation oronehour, whichever is the lesser time period.

TABLE 404(a) 

### Maximum Concentration Maximum Concentration ofParticulate ofParticulate Matter Volume Discharged Matter"Allowed in VolumeDischarged Allowed in Discharged

Calculated as Dry Discharged Gas Calculated as Dry Gas Gas Calculated as Dry Gas Gas Calculated as Dry At Standard Conditions at At Standard Gas at Standard Standard Conditions Conditions Conditions Cubic Cubic Milligrams Grains per Cubic Cubic Milligrams Grains per meters feet per Cubic Foot meters feet per Cubic

Per Per Cubic PerMinute Per Cubic Meter Foot Minute Minute Meter Minute

25 or 883 450 0.196 900 31780 118 0.0515 or less less

30 1059 420 .183 1000 35310 113 .0493 35 1236 397 .173 1100 38850 109 .0476 40 1413 377 .165 1200 42380 106 .0463 45 1589 361 .158 1300 45910 102 .0445

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178



## FACILITYPERMIT TO OPERATE Appendix B Page: 16 Facilitv ID: 800074 Revision#: 7 Date: January 14, 2015


## LACITY.DWPHAYNES GENERATING STATION

VolumeDischarged

Calculated as Dry Gas At Standard Conditions Cubic Cubic meters feet

Per Per Minute Minute



### 50 1766 60 2119 70 2472 80 2825 90 3178 100 3531 125 4414 150 5297 175 6180 200 7063 250 8829 300 10590 350 12360 400 14130 450 15890 APPENDIX B: RULE EMISSION LIMITS [RULE 404 02-07-1986] 

### Maximum Concentration ofParticulate Matter"Allowed in VolumeDischarged

Discharged Gas Calculated as Dry Gas Calculated as Dry At Standard Conditions

Gas at Standard Conditions Milligrams Grains per Cubic Cubic per Cubic Foot meters feet Cubic PerMinute Per Meter Minute



### 347 .152 1400 49440 324 .141 1500 52970 306 .134 1750 61800 291 .127 2000 70630 279 .122 2250 79460 267 .117 2500 88290 246 .107 3000 105900 230 .100 4000 141300 217 .0947 5000 176600 206 .0900 6000 211900 190 .0830 8000 282500 177 .0773 10000 353100 167 .0730 15000 529700 159 .0694 20000 706300 152 .0664 25000 882900 Maximum Concentration ofParticulateMatter Allowed in Discharged Gas Calculated as Dry Gas at Standard Conditions Milligrams Grains per per Cubic Cubic Meter Foot 

### 100 .0437

97 .0424 92 .0402 87 .0380 83 .0362 80 .0349 75 .0327 67 .0293 62 .0271 58 .0253 52 .0227 48 .0210 41 .0179 37 .0162 34 .0148

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMIT TOOPERATE Appendix B Page: 17 Facility ID· 800074 Revision#: 7 Date: January 14, 2015


## LACITY.DWPHAYNES GENERATING STATION

Volume Discharged

Calculated as Dry Gas At Standard Conditions Cubic Cubic meters feet

Per Per Minute Minute 

### 500 17660 600 21190 700 24720 800 28250 APPENDIXB: RULE EMISSION LIMITS [RULE 404 02-07-1986) 

### Maximum Concentration ofParticulate Matter"Allowed in VolumeDischarged

Discharged Gas Calculated asDry Gas Calculated as Dry At Standard Conditions

Gas at Standard Conditions Milligrams Grains per Cubic Cubic per Cubic Foot meters feet Cubic PerMinute Per Meter Minute



### 146 .0637 30000 1059000 137 .0598 40000 1413000 129 .0563 50000 1766000 123 .0537 70000 2472000 ormore ormore Maximum Concentration ofParticulateMatter Allowed in Discharged Gas Calculated asDry Gas at Standard Conditions Milligrams Grains per per Cubic Cubic Meter Foot


### 32 .0140 28 .0122 26 .0114 23 .0100

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTO OPERATE Appendix B Page· 18 Facilitv ID: 800074 Revision#· 7 Date: January 14,2015


## LACITY.DWPHAYNES GENERATING STATION
APPENDIX B: RULE EMISSION LIMITS [RULE 405 02-07-1986) 

### The operator shall not discharge into the atmosphere from this equipment, solid particulate matter including lead and lead compounds in excess ofthe rate shown in Table405(a). Where the process weight per hour is between figures listed in the table, the exact weight ofpermitted discharge shall bedetermined by linearinterpolation.
Forthe purposes ofthis rule, emissions shall be averaged overone complete cycle of operation orone hour, whichever is the lessertimeperiod.

TABLE405(a) 

### Maximum Discharge Maximum Discharge Rate Rate Allowed for Solid Allowed for Solid Particulate Matter Process Weight ParticulateMatter Process Weight (AggregateDischarged PerHour (Aggregate PerHour From All points of Discharged From All Process Points of Process Kilograms Pounds Kilograms Pounds Kilograms Pounds Kilograms Pounds PerHour Per Hour PerHour PerHour PerHour PerHour PerHour PerHour

100 or 220 or 0.450 0.99 9000 19840 5.308 11.7 less less 150 331 0.585 1.29 10000 22050 5.440 12.0 200 441 0.703 1.55 12500 27560 5.732 12.6 250 551 0.804 1.77 15000 33070 5.982 13.2 300 661 0.897 1.98 17500 38580 6.202 13.7 350 772 0.983 2.17 20000 44090 6.399 14.1 400 882 1.063 2.34 25000 55120 6.743 14.9 450 992 1.138 2.51 30000 66140 7.037 15.5 500 1102 1.209 2.67 35000 77160 7.296 16.1 600 1323 1.340 2.95 40000 88180 7.527 16.6

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMIT TOOPERATE Appendix 8 Page: I9 Facilitv ID: 800074 Revision#: 7 Date: January 14. 2015


## LACITY.DWPHAYNES GENERATING STATION

Process Weight PerHour

Kilograms Pounds PerHour PerHour

700 1543 800 1764 900 1984 1000 2205 1250 2756 1500 3307 1750 3858 2000 4409 2250 4960 2500 5512 2750 6063 3000 6614 3250 7165 3600 7716 4000 8818 4500 9921 5000 11020 6000 13230 7000 15430 8000 17640 APPENDIX B: RULE EMISSION LIMITS [RULE 405 02-07-1986] 

### Maximum Discharge Rate Allowedfor Solid ParticulateMatter Process Weight (Aggregate PerHour Discharged From All Points of Process Kilograms Pounds Kilograms Pounds PerHour PerHour PerHour PerHour 1.461 3.22 45000 99210 1.573 3.47 50000 110200 1.678 3.70 60000 132300 1.777 3.92 70000 154300 2.003 4.42 80000 176400 2.206 4.86 90000 198400 2.392 5.27 100000 220500 2.563 5.65 125000 275600 2.723 6.00 150000 330700 2.874 6.34 175000 385800 3.016 6.65 200000 440900 3.151 6.95 225000 496000 3.280 7.23 250000 551200 3.404 7.50 275000 606300 3.637 8.02 300000 661400 3.855 8.50 325000 716500 4.059 8.95 350000 771600 4.434 9.78 400000 881800 4.775 10.5 450000 992100 5.089 11.2 500000 1102000 

### ormore ormore Maximum DischargeRate Allowed for Solid ParticulateMatter (Aggregate Discharged From All points of Process Kilograms Pounds PerHour PerHour 7.738 17.1 7.931 17.5 8.277 18.2 8.582 18.9 8.854 19.5 9.102 20.1 9.329 20.6 9.830 21.7 10.26 22.6 10.64 23.5 10.97 24.2 11.28 24.9 11.56 25.5 11.82 26.1 12.07 26.6 12.30 27.1 12.51 27.6 12.91 28.5 13.27 29.3 13.60 30.0

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTO OPERATE LACITY.DWPBAYNES GENERATING STATION
APPENDIX B: RULE EMISSION LIMITS [40CFR 72 -Acid Rain Provisions 11-24-1997) Appendix B Page: 20 Facilitv ID: 800074 Revision#: 7 Date: January 14, 2015

I. A Title V permit revision is not required for emission increases that are authorized by allowances acquired underthe Acid Rain Program, provided that the increases do not trigger a Title V permit revision under any other applicable requirement. [70.6 (a)(4)(ii)] MonitoringRequirements 2. The owners and operators and, to the extent applicable, the designated representative ofeach affected source and each affected unit at the source shall comply with the monitoring requirements as provided in 40 CFR Parts 74, 75, and 76. [40 CFR 72.50, 72.31, 72.9(b)(l)) 3. The emissions measurements recorded and reported in accordance with 40 CFR Part 75 shall be used to determine compliance by the unit with the acid rain emissions limitations and emissions reduction requirements for sulfur dioxide (S02 ) under the AcidRain Program. [40 CFR72.9(b)(2), 40 CFR75.2) 4. The requirements of40 CFRParts 74 and 75 shall not affect the responsibility ofthe operatorto monitor emissions ofotherpollutants orother emissions characteristics at the unitunderotherapplicable requirements and otherprovisions ofthis permit. [40 CFR72.9(b)(3), 40 CFR72.5) SulfurDioxideRequirements 5. The owners and operators ofeach sourceand each affected unit atthe source shall: (A) Hold allowances, as ofthe allowance transfer deadline, in the unit's compliance subaccount (after deductions under 40 CFR Part 73, Section 73.34(C)) not less than the total annual emissions ofS02 for the previous calendar year from the unit; and, [40 CFR72.9(c)(i)], (B) Comply with the applicable acid rain emissions limitations for SOi.(40 CFR 72.9(c)(ii)) 6. Each ton of S02emitted in excess ofthe acid rain emissions limitations for sulfur dioxide shall constitute a separateviolation oftheAct. [40 CFR 72.9(g)(7))

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMIT TO O.PERATE LACITY.DWPHAYNES GENERATING STATION
APPENDIX B: RULE EMISSION LIMITS (40CFR 72 -Acid Rain Provisions 11-24-1997) Appendix B Page: 21 Facilitv ID: 800074 Revision#: 7 Date: January 14, 2015

7. S02 allowances shall be held in, deducted from, or transferred among allowance tracking system accounts in accordance with the Acid Rain Program. [ 40 CFR 72.9(g)(4)) 8. A S02 allowance shall not be deducted in order to comply with the requirements under paragraph 41 (A) ofthe S02 requirements prior to the calendar year for which the allowance was allocated. [40 CFR72.9(g)(S)) 9. An affected unit shall be subject to the S02 requirements under the Acid Rain Program as follows:[40 CFR72.6(a)] (A) Starting January 1, 2000, an affected unit under 40 CFR Part 72, Section 72.6(a)(2); or [40 CFR72.6(a)(2)) (B) Starting on the later ofJanuary I, 2000 orthe deadline for monitor certification under 40 CFR Part 75, an affected unit under 40 CFR Part 72, Section 72.6(a)(3). [40CFR72 6(a)(3)) I0. An allowance allocated by theEPA administrator under the Acid Rain Program is a limited authorization to emit S02 in accordance with the Acid Rain Program. No provision ofthe Acid Rain Program, the acid rain permit application, the acid rain permit, or the written exemption under 40 CFR Part 72, Sections 72.7, 72.8, or 72.14, and no provision oflaw shall beconstrued to limit the authority ofthe United States toterminate orlimit suchauthorization. [40 CFR72.9 (c)(6)) 11. An allowance allocated by the EPA Administrator under the Acid Rain Program does notconstitute a propertyright. [40 CFR72.9(c)(7)) Excess Emissions Reguirements 12. The designated representative of an affected unit that has excess emissions in any calendar year shall submit a proposed offset plan, as required under40 CFRPart 77. [40 CFR72 9(e))

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTO OPERATE LA CITY.DWPHAYNES GENERATING STATION
APPENDIX 8: RULE EMISSION LIMITS (40CFR 72 -Acid Rain Provisions 11-24-1997) Appendix B Page: 22 Facilitv ID: 800074 Revision#: 7 Date: January 14.2015

13. The owners and operators of an affected unit that has excess emissions in any calendaryearshall: [40 CFR72.9(e)(2)] (A) Pay without demand the penalty required, and pay upon demand the interest on thatpenalty, as required by 40 CFRPart77; and[40 CFR72.9(e)(2)(i)] (B) Comply with the terms ofan approved offset plan, as required by 40 CFR Part 77. [40 CFR72.9(e)(2)(ii)] 

### Recordkeeping andReportingReguirements 14. Unless otherwise provided, the owners and operators ofthe source and each affected unit atthe source that are subjectto the acid rain provisions underTitleIV shall keep on site at the source each ofthe following documents for a period offive years from the date the document is created. This period may beextended for cause, at any time prior to the end offive years, in writing by the EPA Administrator or the Executive Officer: [40 CFR72.9(t)(I)] (A) The certificate ofrepresentation for the designated representative for the source and each affected unit at the source and all documents that demonstrate the truth of the statements in the certificate ofrepresentation, in accordance with 40 CFR72.24; provided that the certificate and documents shall be retained on site at the source beyond such five year period until such documents are superseded because ofthe submission of a new certificate of representation changing the designated representative; [40 CFR72.9(f)(l)(i)] (B) All emissions monitoring information, in accordance with 40 CFR Part 75; [40 CFR72.9(t)(i)(ii)] (C) Copies ofall reports, compliance certifications, and other submissions and all records madeorrequired underthe AcidRain Program; and, [40 CFR72.9(f)(l)(iii)] (D) Copies ofall documents used to complete an acid rain permit application and any other submission under the Acid Rain Program or to demonstrate compliance with the requirements ofthe Acid Rain Program. [40 CFR72.9(t)(l)(iv)]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar. CA 91765-4178


## FACILITYPERMIT TOOPERATE LACITY.DWPHAYNES GENERATING STATION
APPENDIX B: RULE EMISSION LIMITS [40CFR 72 -AcidRaio Provisions 

### 11-24-1997) Appendix B Page: 23 Facilitv ID: 800074 Revision#: 7 Date: January 14,2015



### 1S. 

### The designated representative of an affected source and each affected unit at the source shall submitthe reports and compliance certifications required under the Acid Rain Program, including those under 40 CFR Part 72 Subpart I 

### and 40 CFRPart 75. [40 CFR72.9(t)(2)] Liability 16. Any person who knowingly violates any requirement or prohibition ofthe Acid Rain Program, a complete acid rain permit application, an acid rain permit, or a written exemption under 40 CFR Part 72, Sections 72.7, 72.8, or 72.14, including any requirement for the payment of any penalty owed to the United States, shall be subjectto enforcementpursuant to Section l 13(c) oftheAct. [40 CFR72.9 (g)(l)] 17. Any person who knowingly makes a false, material statement in any record, submission, or report under the Acid Rain Program shall be subject to criminal enforcement pursuant to Section l 13(c) ofthe Act and 18 U.S.C. 1001. [40 CFR 72.9 (g)(2)] 18. No permit revision shall excuse any violation ofthe requirements ofthe Acid Rain Program that occurs prior to the date that the revision takes effect. [40 CFR 72.9 (g)(3)] 

### 19. Each affected source and each affected unit shall meet the requirements ofthe Acid Rain Program. [40 CFR72.9 (g)(4)] 20. Any provision ofthe Acid Rain Program thatapplies to an affected source (including a provision applicable to the designated representative ofan affected source) shall also apply to the owners and operators ofsuch source and ofthe affected units at the source. [40 CFR72.9 (g)(S)]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMITTO OPERATE LA CITY.DWPBAYNES GENERATING STATION
APPENDIX B: RULE EMISSION LIMITS [40CFR 72 -Acid Rain Provisions 11-24-19971 Appendix B Page: 24 Facility ID: 800074 Revision#: 7 Date: Jam.1ary 14, 2015

21. Any provision ofthe Acid Rain Program that applies to an affected unit (including a provision applicable to the designated representative ofan affected unit) shall also apply to the owners and operators ofsuch unit. Except 

### as provided under 40 CFR Part 72, Section 72.44 (Phase II repowering extension plans) and 40 CFR Part 76, Section 76.11 (NOx averaging plans), and except with regard to the requirements applicable to units with a common stack under 40 CFR Part 75 (including 40 CFR Part 75, Sections 75.16, 75.17, and 75.18), the owners and operators and the designated representative ofone affected unit shall not be liable for any violation by any other affected unit ofwhich they are not owners or operators or the designated representative and that is located at a source of which they are not owners or operators orthe designated representative. [40 CFR72.9 (g)(6)] 22. Each violation ofa provision of40 CFR Parts 72, 73, 74, 75, 76, 77, and 78 by an affected source or affected unit, or by an owner or operator or designated representative of such source or unit, shall be a separate violation ofthe Act. [ 40 CFR 72.9 (g)(7)] Effecton OtherAuthorities 23. No provision ofthe Acid Rain Program, an acid rain permit application, an acid rain permit, or a written exemption under 40 CFR Part 72, Sections 72.7, 72.8, or 72.14 shall be construed as: [40 CFR72.9 (h)] (A) Exceptas expressly provided in Title IV ofthe Act, exempting or excluding the owners and operators and, to the extent applicable, the designated representative of an affected source or affected unit from compliance with any other provision ofthe Act, including the provisions of Title I of the Act relating to applicable National Ambient Air Quality Standards or state implementation plans; [40 CFR72.9 (h)(l)] (B) Limiting the numberofallowances a unit can hold;

### provided, that the number of allowances held by the unit shall not affect the source's obligation to comply with any otherprovisions oftheAct; [40 CFR72.9 (h)(2)]

### South Coast Air Quality Management District 21865 Copley Drive, Diamond Bar, CA 91765-4178


## FACILITYPERMIT TOOPERATE LA CITY.DWPHAYNES GENERATING STATION
APPENDIXB: RULE EMISSIONLIMITS [40CFR 72 -Acid Rain Provisions 11-24-1997) (C) Requiring a change ofany kind in any state lawregulating electric utility rates and charges, affecting any state lawregarding such state regulation, or limiting such state regulation, including any prudence review requirements under such state law; [40 CFR72.9 (h)(3)] (D) Modifying the Federal Power Act or affecting the authority of the Federal Energy Regulatory Commission under the Federal Power Act; or, [40 CFR 72.9 (h)(4)] (E) Interfering with or impairing any program for competitive bidding for power supply in a statein which such program is established. [40 CFR72.9 (h)(5)] Appendix B Page: 25 Facilitv ID: 800074 Revision #: 7 Date: January 14,2015