Name:

Title:

Company:

Sign Date:

Name:

Title:

Company:

Sign Date:

Permitted Facility Representative / Date Testing Company Representative / Date

Final Test Report 

for

/ /

Based on information and belief formed 

after reasonable inquiry, I certify that the 

statements and information in this test 

report are true, accurate, and complete.

I have reviewed all testing details and 

results in this test report and hereby 

certify that the test report is authentic 

and accurate.

Friday, February 11, 2011 Page 1 of 33
Facility Information:

ENTERGY MS BAXTER WILSON POWE

770 Kemp Bottom Road

Vicksburg MS 39180

Contact: Theordore Chenet

Phone: 281-297-3313

Fax: 281-297-3013

Email: TCHENET@entergy.com

Testing Company:

METCO Environmental

3226 Commander Blvd.

Carrollton TX 75006

Contact: Ned Shappley

Phone: 972-931-7127

Fax: 972-931-8398

Email: nshappley@metcoenv.com

Air Permit Number: Permitted Source ID/Name:

Boiler ID Unit Number 1 Stack

Permitted Maximum Process Rate:

N/A

Max. Normal Operation Process Rate:

N/A

Target Process Test Rate

N/A

Description of the source (including control equipment). Please see the attachments for source or

 process flow diagram:

This description should describe the process and associated controls to differentiate this facility from, or document 

similarity with others of same SCC.

Industry/SCC/NAIS 221112

Sampling Location Information:

Test Parameter Information:

AFS #: 110000376548 FRS #: 110000376548

SCC / Description 10102101 External Combustion Boilers - Electric Generation - Other Oil - 

All 

The following state and federal regulations that apply to the proposed testing:

Location

Round

Duct

Diam.

Distance from 

upstream dist.

Distance from

downstream dist.

Number of

Traverse Ports

Equiv. 

Diam

Min.Travers 

Points

Rect. Duct 

Length /Width

Stack Exit 228 0 0 228 2508 2280 4 12

Exhaust Duct 0 512 216 304 152 196 1 3

Target

Parameter 

Test

Method

Number of

Test Runs

Test Run

Duration

Sample 

Location Points Comments

Stack Exit Carbon Monoxide Method 10 3 420 0

Stack Exit 2,3,7,8-TCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDD Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDD Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDD Method 23 3 480 0

Friday, February 11, 2011 Page 2 of 33
Stack Exit 1,2,3,4,6,7,8-HpCDD Method 23 3 480 0

Stack Exit OCDD Method 23 3 480 0

Stack Exit 2,3,7,8-TCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8-PeCDF Method 23 3 480 0

Stack Exit 2,3,4,7,8-PeCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 2,3,4,6,7,8-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,7,8,9-HxCDF Method 23 3 480 0

Stack Exit 1,2,3,4,6,7,8-HpCDF Method 23 3 480 0

Stack Exit 1,2,3,4,7,8,9-HpCDF Method 23 3 480 0

Stack Exit OCDF Method 23 3 480 0

Stack Exit Other TCDD Method 23 3 480 0

Stack Exit Other PeCDD Method 23 3 480 0

Stack Exit Other HxCDD Method 23 3 480 0

Stack Exit Other HpCDD Method 23 3 480 0

Stack Exit Other TCDF Method 23 3 480 0

Stack Exit Other PeCDF Method 23 3 480 0

Stack Exit Other HxCDF Method 23 3 480 0

Stack Exit Other HpCDF Method 23 3 480 0

Stack Exit Total Dioxins Method 23 3 480 0

Stack Exit Total Furans Method 23 3 480 0

Stack Exit 3,3',4,4'-TCB (PCB77) Method 23 3 480 0

Stack Exit 3,4,4',5-TCB (PCB81) Method 23 3 480 0

Stack Exit 2,3,3',4,4'-PeCB (PCB105) Method 23 3 480 0

Stack Exit 2,3,4,4',5-PeCB (PCB114) Method 23 3 480 0

Stack Exit 2,3',4,4',5-PeCB (PCB118) Method 23 3 480 0

Stack Exit 2',3,4,4',5-PeCB (PCB123) Method 23 3 480 0

Stack Exit 3,3',4,4',5-PeCB (PCB126) Method 23 3 480 0

2,3,3',4,4',5/2,3,3',4,4',5'-

HxCB (PCBs156/157)

Stack Exit Method 23 3 480 0

Stack Exit 2,3',4,4',5,5'-HxCB (PCB167) Method 23 3 480 0

Stack Exit 3,3',4,4',5,5'-HxCB (PCB169) Method 23 3 480 0

2,3,3',4,4',5,5'-HpCB 

(PCB189)

Stack Exit Method 23 3 480 0

Total organic compounds 

(TOC) as Propane

Stack Exit Method 25A 3 180 0

Inorganic (Aqueous) 

Condensible Part.

OTM - 27/28 3 366 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Filterable PM2.5 OTM - 27/28 3 366 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Organic Condensible 

Particulate

OTM - 27/28 3 366 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total PM2.5 OTM - 27/28 3 366 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Total Particulate OTM - 27/28 3 366 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Friday, February 11, 2011 Page 3 of 33
The following describes any modifications and/or deviations to the applicable test 

methods. If alternative methods were requested, see the attachments for documentation 

of request AND approval, including dates.

Two of the test ports at the stack were unable to be sampled out of due to testing location obstructions. The samples 

were taken out of the two available test ports. Six total points were sampled out of the two existing ports.

Method 26 was modified to collect HCN with the HCL and HF.The concentration of the sodium hydroxide solution 

used was increased from 0.1 N to 6N , an additional impinger containing sodium hydroxide was added to the train 

(three impingers instead of two), the pH of the impinger solutions was

monitored periodically throughout the sample run. This modification was addressed on the Uticility ICR website in 

the Frequently Asked Questions area (Question Test-025). At the time of testing, this modification was still approved.

The reference method monitors, HCL, HF, HCN, and VOST sampling was performed at the Exhaust Outlet Duct 

located at the base of the stack. The sampling ports used were directly above the plant CEMS monitor location.

Filterable Particulate OTM - 27/28 3 366 0 Use only for dry 

stacks. Delete Method 

5/OTM28 tests.

Stack Exit

Stack Exit Filterable Particulate Method 29 3 240 0

Stack Exit Beryllium Method 29 3 240 0

Stack Exit Cadmium Method 29 3 240 0

Stack Exit Chromium Method 29 3 240 0

Stack Exit Lead Method 29 3 240 0

Stack Exit Mercury Method 29 3 240 0

Stack Exit Selenium Method 29 3 240 0

Stack Exit Phosphorus (yellow or white) Method 29 3 240 0

Stack Exit Antimony Method 29 3 240 0

Stack Exit Cobalt Method 29 3 240 0

Stack Exit Manganese Method 29 3 240 0

Stack Exit Arsenic Method 29 3 240 0

Stack Exit Nickel Method 29 3 240 0

Stack Exit Co2 Method 3A CO2 3 420 0

Stack Exit O2 Method 3A O2 3 420 0

Stack Exit Sulfur Dioxide Method 6C 3 420 0

Stack Exit Nitrogen oxides (NOx) Method 7E 3 420 0

Friday, February 11, 2011 Page 4 of 33
Sampling / Stack Data Results Summary

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 2:12:00 PM 7:25:00 

AM

2:35:00 AM

Run Finish Time 11:50:00 PM 3:34:00 PM 1/1/1900 

2:15:00 AM

Net Run Time, minutes 480 480 480

Dry Gas Meter Volume Sampled, dscf 315.388 322.762 297.956 312.035

Moisture Content of Stack Gas, % 9.07 9.89 10.12 9.693

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Carbon Dioxide, % 10.5 10.4 10.5 10.467

Oxygen, % 7.7 7.6 7.7 7.667

Average Stack Gas Temperature, °F 219.63 232.44 225.94 226.003

Dry Volumetric Flow Rate, dry scfm 812,312.6 795,401.1 775,118.8 794,277.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,164,283.5 1,169,727.2 1,132,471.5 1,155,494.06

7

Percent Isokinetic of Sampling Rate, % 99.1 103.6 98.1 100.267

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Friday, February 11, 2011 Page 5 of 33
Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Friday, February 11, 2011 Page 6 of 33
Location Stack Exit - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, February 11, 2011 Page 7 of 33
Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Fuel Type

Fw

Fc

Friday, February 11, 2011 Page 8 of 33
Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Run Time, minutes

Dry Gas Meter Volume Sampled, dscf

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Carbon Dioxide, %

Oxygen, %

Average Stack Gas Temperature, °F

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

F-Factor, dscfm/MMBtu @ %O2

Fw

Fc

Friday, February 11, 2011 Page 9 of 33
Emissions Summary

Location: Stack Exit - Method 10

Compound: Carbon Monoxide

Average

Run 1 2 3

Elb/hr 0.00E+00 0.00E+00 -1.12E+00 -0.373

lb/mmBtuO2 0.00E+00 0.00E+00 -3.37E-04 0.000

ppm 0.00E+00 0.00E+00 -3.19E-01 -0.106

ppm@7%O2 0.00E+00 0.00E+00 -3.35E-01 -0.112

Location: Stack Exit - Method 23

Compound: 1,2,3,4,6,7,8-HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000072 0.0000000057 0.0000000043 0.000

Elb/hr 2.45E-09 1.86E-09 1.48E-09 0.000

lb/mmBtuO2 7.32E-13 5.62E-13 4.63E-13 0.000

ng/dscm 8.06E-04 6.24E-04 5.10E-04 0.001

ng/dscm@7%O2 8.49E-04 6.52E-04 5.37E-04 0.001

Compound: 1,2,3,4,6,7,8-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000042 0.0000000063 0.000000004 0.000

Elb/hr 1.43E-09 2.05E-09 1.38E-09 0.000

lb/mmBtuO2 4.27E-13 6.21E-13 4.31E-13 0.000

ng/dscm 4.70E-04 6.89E-04 4.74E-04 0.001

ng/dscm@7%O2 4.95E-04 7.20E-04 4.99E-04 0.001

Compound: 1,2,3,4,7,8,9-HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000027 0.0000000034 0.0000000018 0.000

Elb/hr 9.20E-10 1.11E-09 6.19E-10 0.000

lb/mmBtuO2 2.75E-13 3.35E-13 1.94E-13 0.000

ng/dscm 3.02E-04 3.72E-04 2.13E-04 0.000

ng/dscm@7%O2 3.18E-04 3.89E-04 2.24E-04 0.000

Compound: 1,2,3,4,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.000000002 0.0000000013 0.000

Elb/hr 5.79E-10 6.52E-10 4.47E-10 0.000

lb/mmBtuO2 1.73E-13 1.97E-13 1.40E-13 0.000

ng/dscm 1.90E-04 2.19E-04 1.54E-04 0.000

ng/dscm@7%O2 2.00E-04 2.29E-04 1.62E-04 0.000

Compound: 1,2,3,4,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000028 0.000000004 0.0000000022 0.000

Elb/hr 9.54E-10 1.30E-09 7.57E-10 0.000

Friday, February 11, 2011 Page 10 of 33
lb/mmBtuO2 2.85E-13 3.95E-13 2.37E-13 0.000

ng/dscm 3.14E-04 4.38E-04 2.61E-04 0.000

ng/dscm@7%O2 3.31E-04 4.58E-04 2.75E-04 0.000

Compound: 1,2,3,6,7,8-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.0000000019 0.0000000013 0.000

Elb/hr 5.79E-10 6.19E-10 4.47E-10 0.000

lb/mmBtuO2 1.73E-13 1.87E-13 1.40E-13 0.000

ng/dscm 1.90E-04 2.08E-04 1.54E-04 0.000

ng/dscm@7%O2 2.00E-04 2.17E-04 1.62E-04 0.000

Compound: 1,2,3,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000022 0.0000000018 0.0000000008 0.000

Elb/hr 7.50E-10 5.87E-10 2.75E-10 0.000

lb/mmBtuO2 2.24E-13 1.78E-13 8.61E-14 0.000

ng/dscm 2.46E-04 1.97E-04 9.48E-05 0.000

ng/dscm@7%O2 2.59E-04 2.06E-04 9.98E-05 0.000

Compound: 1,2,3,7,8,9-HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000017 0.000000002 0.0000000013 0.000

Elb/hr 5.79E-10 6.52E-10 4.47E-10 0.000

lb/mmBtuO2 1.73E-13 1.97E-13 1.40E-13 0.000

ng/dscm 1.90E-04 2.19E-04 1.54E-04 0.000

ng/dscm@7%O2 2.00E-04 2.29E-04 1.62E-04 0.000

Compound: 1,2,3,7,8,9-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000033 0.0000000014 0.00000000084 0.000

Elb/hr 1.12E-09 4.56E-10 2.89E-10 0.000

lb/mmBtuO2 3.36E-13 1.38E-13 9.04E-14 0.000

ng/dscm 3.70E-04 1.53E-04 9.96E-05 0.000

ng/dscm@7%O2 3.90E-04 1.60E-04 1.05E-04 0.000

Compound: 1,2,3,7,8-PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000043 0.0000000048 0.0000000015 0.000

Elb/hr 1.46E-09 1.56E-09 5.16E-10 0.000

lb/mmBtuO2 4.37E-13 4.73E-13 1.61E-13 0.000

ng/dscm 4.82E-04 5.25E-04 1.78E-04 0.000

ng/dscm@7%O2 5.08E-04 5.49E-04 1.87E-04 0.000

Compound: 1,2,3,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000044 0.0000000045 0.0000000012 0.000

Elb/hr 1.50E-09 1.47E-09 4.13E-10 0.000

Friday, February 11, 2011 Page 11 of 33
lb/mmBtuO2 4.48E-13 4.44E-13 1.29E-13 0.000

ng/dscm 4.93E-04 4.92E-04 1.42E-04 0.000

ng/dscm@7%O2 5.19E-04 5.14E-04 1.50E-04 0.000

Compound: 2,3,3',4,4',5,5'-HpCB (PCB189)

Average

RunNumber 1 2 3

Mass_mg 0.0000000161 0.0000000148 0.0000000125 0.000

Elb/hr 5.49E-09 4.82E-09 4.30E-09 0.000

lb/mmBtuO2 1.64E-12 1.46E-12 1.35E-12 0.000

ng/dscm 1.80E-03 1.62E-03 1.48E-03 0.002

ng/dscm@7%O2 1.90E-03 1.69E-03 1.56E-03 0.002

Compound: 2,3,3',4,4',5/2,3,3',4,4',5'-HxCB (PC

Average

RunNumber 1 2 3

Mass_mg 0.0000001036 0.0000000632 0.0000000472 0.000

Elb/hr 3.53E-08 2.06E-08 1.62E-08 0.000

lb/mmBtuO2 1.05E-11 6.23E-12 5.08E-12 0.000

ng/dscm 1.16E-02 6.92E-03 5.60E-03 0.008

ng/dscm@7%O2 1.22E-02 7.23E-03 5.90E-03 0.008

Compound: 2,3,3',4,4'-PeCB (PCB105)

Average

RunNumber 1 2 3

Mass_mg 0.0000002318 0.0000000836 0.0000000234 0.000

Elb/hr 7.90E-08 2.73E-08 8.05E-09 0.000

lb/mmBtuO2 2.36E-11 8.25E-12 2.52E-12 0.000

ng/dscm 2.60E-02 9.15E-03 2.77E-03 0.013

ng/dscm@7%O2 2.74E-02 9.56E-03 2.92E-03 0.013

Compound: 2,3',4,4',5,5'-HxCB (PCB167)

Average

RunNumber 1 2 3

Mass_mg 0.0000000179 0.0000000168 0.000000012 0.000

Elb/hr 6.10E-09 5.48E-09 4.13E-09 0.000

lb/mmBtuO2 1.82E-12 1.66E-12 1.29E-12 0.000

ng/dscm 2.00E-03 1.84E-03 1.42E-03 0.002

ng/dscm@7%O2 2.11E-03 1.92E-03 1.50E-03 0.002

Compound: 2,3,4,4',5-PeCB (PCB114)

Average

RunNumber 1 2 3

Mass_mg 0.0000000152 0.0000000133 0.0000000113 0.000

Elb/hr 5.18E-09 4.34E-09 3.89E-09 0.000

lb/mmBtuO2 1.55E-12 1.31E-12 1.22E-12 0.000

ng/dscm 1.70E-03 1.46E-03 1.34E-03 0.002

ng/dscm@7%O2 1.79E-03 1.53E-03 1.41E-03 0.002

Compound: 2,3',4,4',5-PeCB (PCB118)

Average

RunNumber 1 2 3

Mass_mg 0.0000006047 0.0000002175 0.0000000824 0.000

Elb/hr 2.06E-07 7.09E-08 2.84E-08 0.000

Friday, February 11, 2011 Page 12 of 33
lb/mmBtuO2 6.15E-11 2.15E-11 8.87E-12 0.000

ng/dscm 6.77E-02 2.38E-02 9.77E-03 0.034

ng/dscm@7%O2 7.13E-02 2.49E-02 1.03E-02 0.036

Compound: 2',3,4,4',5-PeCB (PCB123)

Average

RunNumber 1 2 3

Mass_mg 0.0000000168 0.0000000148 0.0000000126 0.000

Elb/hr 5.72E-09 4.82E-09 4.34E-09 0.000

lb/mmBtuO2 1.71E-12 1.46E-12 1.36E-12 0.000

ng/dscm 1.88E-03 1.62E-03 1.49E-03 0.002

ng/dscm@7%O2 1.98E-03 1.69E-03 1.57E-03 0.002

Compound: 2,3,4,6,7,8-HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000015 0.0000000016 0.00000000097 0.000

Elb/hr 5.11E-10 5.22E-10 3.34E-10 0.000

lb/mmBtuO2 1.53E-13 1.58E-13 1.04E-13 0.000

ng/dscm 1.68E-04 1.75E-04 1.15E-04 0.000

ng/dscm@7%O2 1.77E-04 1.83E-04 1.21E-04 0.000

Compound: 2,3,4,7,8-PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000032 0.0000000025 0.0000000021 0.000

Elb/hr 1.09E-09 8.15E-10 7.23E-10 0.000

lb/mmBtuO2 3.25E-13 2.47E-13 2.26E-13 0.000

ng/dscm 3.58E-04 2.74E-04 2.49E-04 0.000

ng/dscm@7%O2 3.77E-04 2.86E-04 2.62E-04 0.000

Compound: 2,3,7,8-TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000004 0.0000000046 0.0000000028 0.000

Elb/hr 1.36E-09 1.50E-09 9.64E-10 0.000

lb/mmBtuO2 4.07E-13 4.54E-13 3.01E-13 0.000

ng/dscm 4.48E-04 5.03E-04 3.32E-04 0.000

ng/dscm@7%O2 4.72E-04 5.26E-04 3.50E-04 0.000

Compound: 2,3,7,8-TCDF

Average

RunNumber 1 2 3

Mass_mg 0.0000000031 0.0000000056 0.0000000017 0.000

Elb/hr 1.06E-09 1.83E-09 5.85E-10 0.000

lb/mmBtuO2 3.15E-13 5.52E-13 1.83E-13 0.000

ng/dscm 3.47E-04 6.13E-04 2.02E-04 0.000

ng/dscm@7%O2 3.65E-04 6.41E-04 2.13E-04 0.000

Compound: 3,3',4,4',5,5'-HxCB (PCB169)

Average

RunNumber 1 2 3

Mass_mg 0.00000002 0.0000000183 0.0000000136 0.000

Elb/hr 6.81E-09 5.97E-09 4.68E-09 0.000

Friday, February 11, 2011 Page 13 of 33
lb/mmBtuO2 2.03E-12 1.81E-12 1.46E-12 0.000

ng/dscm 2.24E-03 2.00E-03 1.61E-03 0.002

ng/dscm@7%O2 2.36E-03 2.09E-03 1.70E-03 0.002

Compound: 3,3',4,4',5-PeCB (PCB126)

Average

RunNumber 1 2 3

Mass_mg 0.0000000179 0.0000000146 0.0000000128 0.000

Elb/hr 6.10E-09 4.76E-09 4.40E-09 0.000

lb/mmBtuO2 1.82E-12 1.44E-12 1.38E-12 0.000

ng/dscm 2.00E-03 1.60E-03 1.52E-03 0.002

ng/dscm@7%O2 2.11E-03 1.67E-03 1.60E-03 0.002

Compound: 3,3',4,4'-TCB (PCB77)

Average

RunNumber 1 2 3

Mass_mg 0.0000000758 0.0000000449 0.0000000153 0.000

Elb/hr 2.58E-08 1.46E-08 5.26E-09 0.000

lb/mmBtuO2 7.71E-12 4.43E-12 1.65E-12 0.000

ng/dscm 8.49E-03 4.91E-03 1.81E-03 0.005

ng/dscm@7%O2 8.94E-03 5.13E-03 1.91E-03 0.005

Compound: 3,4,4',5-TCB (PCB81)

Average

RunNumber 1 2 3

Mass_mg 0.0000000185 0.0000000189 0.0000000146 0.000

Elb/hr 6.30E-09 6.16E-09 5.02E-09 0.000

lb/mmBtuO2 1.88E-12 1.86E-12 1.57E-12 0.000

ng/dscm 2.07E-03 2.07E-03 1.73E-03 0.002

ng/dscm@7%O2 2.18E-03 2.16E-03 1.82E-03 0.002

Compound: OCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000018 0.000000018 0.000000013 0.000

Elb/hr 6.13E-09 5.87E-09 4.47E-09 0.000

lb/mmBtuO2 1.83E-12 1.78E-12 1.40E-12 0.000

ng/dscm 2.02E-03 1.97E-03 1.54E-03 0.002

ng/dscm@7%O2 2.13E-03 2.06E-03 1.62E-03 0.002

Compound: OCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000011 0.0000000097 0.0000000056 0.000

Elb/hr 3.75E-09 3.16E-09 1.93E-09 0.000

lb/mmBtuO2 1.12E-12 9.57E-13 6.03E-13 0.000

ng/dscm 1.23E-03 1.06E-03 6.64E-04 0.001

ng/dscm@7%O2 1.30E-03 1.11E-03 6.99E-04 0.001

Compound: Other HpCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000014 0.0000000057 0.0000000043 0.000

Elb/hr 4.77E-09 1.86E-09 1.48E-09 0.000

Friday, February 11, 2011 Page 14 of 33
lb/mmBtuO2 1.42E-12 5.62E-13 4.63E-13 0.000

ng/dscm 1.57E-03 6.24E-04 5.10E-04 0.001

ng/dscm@7%O2 1.65E-03 6.52E-04 5.37E-04 0.001

Compound: Other HpCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000015 0.0000000063 0.000000004 0.000

Elb/hr 5.11E-09 2.05E-09 1.38E-09 0.000

lb/mmBtuO2 1.53E-12 6.21E-13 4.31E-13 0.000

ng/dscm 1.68E-03 6.89E-04 4.74E-04 0.001

ng/dscm@7%O2 1.77E-03 7.20E-04 4.99E-04 0.001

Compound: Other HxCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000037 0.000000037 0.000000027 0.000

Elb/hr 1.26E-08 1.21E-08 9.29E-09 0.000

lb/mmBtuO2 3.76E-12 3.65E-12 2.91E-12 0.000

ng/dscm 4.14E-03 4.05E-03 3.20E-03 0.004

ng/dscm@7%O2 4.36E-03 4.23E-03 3.37E-03 0.004

Compound: Other HxCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000035 0.000000017 0.000000015 0.000

Elb/hr 1.19E-08 5.54E-09 5.16E-09 0.000

lb/mmBtuO2 3.56E-12 1.68E-12 1.61E-12 0.000

ng/dscm 3.92E-03 1.86E-03 1.78E-03 0.003

ng/dscm@7%O2 4.13E-03 1.94E-03 1.87E-03 0.003

Compound: Other PeCDD

Average

RunNumber 1 2 3

Mass_mg 0.0000000056 0.000000055 0.00000004 0.000

Elb/hr 1.91E-09 1.79E-08 1.38E-08 0.000

lb/mmBtuO2 5.70E-13 5.43E-12 4.31E-12 0.000

ng/dscm 6.27E-04 6.02E-03 4.74E-03 0.004

ng/dscm@7%O2 6.60E-04 6.29E-03 4.99E-03 0.004

Compound: Other PeCDF

Average

RunNumber 1 2 3

Mass_mg 0.00000005 0.000000042 0.000000016 0.000

Elb/hr 1.70E-08 1.37E-08 5.51E-09 0.000

lb/mmBtuO2 5.09E-12 4.14E-12 1.72E-12 0.000

ng/dscm 5.60E-03 4.60E-03 1.90E-03 0.004

ng/dscm@7%O2 5.90E-03 4.81E-03 2.00E-03 0.004

Compound: Other TCDD

Average

RunNumber 1 2 3

Mass_mg 0.000000035 0.000000037 0.000000024 0.000

Elb/hr 1.19E-08 1.21E-08 8.26E-09 0.000

Friday, February 11, 2011 Page 15 of 33
lb/mmBtuO2 3.56E-12 3.65E-12 2.58E-12 0.000

ng/dscm 3.92E-03 4.05E-03 2.84E-03 0.004

ng/dscm@7%O2 4.13E-03 4.23E-03 2.99E-03 0.004

Compound: Other TCDF

Average

RunNumber 1 2 3

Mass_mg 0.000000023 0.000000036 0.000000017 0.000

Elb/hr 7.84E-09 1.17E-08 5.85E-09 0.000

lb/mmBtuO2 2.34E-12 3.55E-12 1.83E-12 0.000

ng/dscm 2.58E-03 3.94E-03 2.02E-03 0.003

ng/dscm@7%O2 2.72E-03 4.12E-03 2.13E-03 0.003

Compound: Total Dioxins

Average

RunNumber 1 2 3

Mass_mg 0.0000001096 0.0000001527 0.0000001083 0.000

Elb/hr 3.73E-08 4.98E-08 3.73E-08 0.000

lb/mmBtuO2 1.11E-11 1.51E-11 1.17E-11 0.000

ng/dscm 1.23E-02 1.67E-02 1.28E-02 0.014

ng/dscm@7%O2 1.30E-02 1.75E-02 1.35E-02 0.015

Compound: Total Furans

Average

RunNumber 1 2 3

Mass_mg 0.000000134 0.000000111 0.0000000576 0.000

Elb/hr 4.57E-08 3.62E-08 1.98E-08 0.000

lb/mmBtuO2 1.36E-11 1.09E-11 6.20E-12 0.000

ng/dscm 1.50E-02 1.21E-02 6.83E-03 0.011

ng/dscm@7%O2 1.58E-02 1.26E-02 7.19E-03 0.012

Location: Stack Exit - Method 25A

Compound: Total organic compounds (TOC) as 

Average

Run 1 2 3

Elb/hr 2.09E+00 0.00E+00 0.00E+00 0.697

lb/mmBtuO2 6.35E-04 0.00E+00 0.00E+00 0.000

ppm 3.77E-01 0.00E+00 0.00E+00 0.126

ppm@7%O2 4.02E-01 0.00E+00 0.00E+00 0.134

Location: Stack Exit - Method 29

Compound: Antimony

Average

RunNumber 1 2 3

Mass_mg 0.229 0.2416 0.2116 0.227

Elb/hr 1.85E-01 1.94E-01 1.77E-01 0.185

lb/mmBtuO2 5.42E-05 5.92E-05 5.41E-05 0.000

mg/dscm 6.06E-02 6.52E-02 6.00E-02 0.062

mg/dscm@7%O2 6.29E-02 6.87E-02 6.27E-02 0.065

Compound: Arsenic

Average

RunNumber 1 2 3

Friday, February 11, 2011 Page 16 of 33
Mass_mg 0.00929 0.01058 0.00848 0.009

Elb/hr 7.52E-03 8.50E-03 7.08E-03 0.008

lb/mmBtuO2 2.20E-06 2.59E-06 2.17E-06 0.000

mg/dscm 2.46E-03 2.85E-03 2.40E-03 0.003

mg/dscm@7%O2 2.55E-03 3.00E-03 2.51E-03 0.003

Compound: Beryllium

Average

RunNumber 1 2 3

Mass_mg 0.001 0.001 0.001 0.001

Elb/hr 8.10E-04 8.03E-04 8.34E-04 0.001

lb/mmBtuO2 2.37E-07 2.45E-07 2.56E-07 0.000

mg/dscm 2.65E-04 2.70E-04 2.84E-04 0.000

mg/dscm@7%O2 2.75E-04 2.84E-04 2.97E-04 0.000

Compound: Cadmium

Average

RunNumber 1 2 3

Mass_mg 0.0015 0.0015 0.0015 0.002

Elb/hr 1.21E-03 1.21E-03 1.25E-03 0.001

lb/mmBtuO2 3.55E-07 3.67E-07 3.83E-07 0.000

mg/dscm 3.97E-04 4.05E-04 4.25E-04 0.000

mg/dscm@7%O2 4.12E-04 4.26E-04 4.44E-04 0.000

Compound: Chromium

Average

RunNumber 1 2 3

Mass_mg 0.02584 0.03101 0.00864 0.022

Elb/hr 2.09E-02 2.49E-02 7.21E-03 0.018

lb/mmBtuO2 6.12E-06 7.60E-06 2.21E-06 0.000

mg/dscm 6.84E-03 8.36E-03 2.45E-03 0.006

mg/dscm@7%O2 7.10E-03 8.80E-03 2.56E-03 0.006

Compound: Cobalt

Average

RunNumber 1 2 3

Mass_mg 0.0453 0.0575 0.0441 0.049

Elb/hr 3.67E-02 4.62E-02 3.68E-02 0.040

lb/mmBtuO2 1.07E-05 1.41E-05 1.13E-05 0.000

mg/dscm 1.20E-02 1.55E-02 1.25E-02 0.013

mg/dscm@7%O2 1.24E-02 1.63E-02 1.31E-02 0.014

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 66.5 84.2 100.9 83.867

Elb/hr 5.39E+01 6.77E+01 8.42E+01 68.600

lb/mmBtuO2 1.57E-02 2.06E-02 2.58E-02 0.021

mg/dscm 1.76E+01 2.27E+01 2.86E+01 22.967

mg/dscm@7%O2 1.83E+01 2.39E+01 2.99E+01 24.033

Compound: Lead

Average

RunNumber 1 2 3

Friday, February 11, 2011 Page 17 of 33
Mass_mg 0.01968 0.0217 0.01663 0.019

Elb/hr 1.59E-02 1.74E-02 1.39E-02 0.016

lb/mmBtuO2 4.66E-06 5.32E-06 4.25E-06 0.000

mg/dscm 5.21E-03 5.85E-03 4.72E-03 0.005

mg/dscm@7%O2 5.40E-03 6.16E-03 4.93E-03 0.005

Compound: Manganese

Average

RunNumber 1 2 3

Mass_mg 0.01774 0.02224 0.01554 0.019

Elb/hr 1.44E-02 1.79E-02 1.30E-02 0.015

lb/mmBtuO2 4.20E-06 5.45E-06 3.97E-06 0.000

mg/dscm 4.69E-03 6.00E-03 4.41E-03 0.005

mg/dscm@7%O2 4.87E-03 6.32E-03 4.61E-03 0.005

Compound: Mercury

Average

RunNumber 1 2 3

Mass_mg 0.00117 0.00116 0.00106 0.001

Elb/hr 9.47E-04 9.32E-04 8.84E-04 0.001

lb/mmBtuO2 2.77E-07 2.84E-07 2.71E-07 0.000

mg/dscm 3.10E-04 3.13E-04 3.01E-04 0.000

mg/dscm@7%O2 3.22E-04 3.30E-04 3.15E-04 0.000

Compound: Nickel

Average

RunNumber 1 2 3

Mass_mg 0.9466 1.04529 0.84329 0.945

Elb/hr 7.67E-01 8.40E-01 7.04E-01 0.770

lb/mmBtuO2 2.24E-04 2.56E-04 2.16E-04 0.000

mg/dscm 2.50E-01 2.82E-01 2.39E-01 0.257

mg/dscm@7%O2 2.59E-01 2.97E-01 2.50E-01 0.269

Compound: Phosphorus (yellow or white)

Average

RunNumber 1 2 3

Mass_mg 0.26807 0.07408 0.26804 0.203

Elb/hr 2.17E-01 5.95E-02 2.24E-01 0.167

lb/mmBtuO2 6.34E-05 1.81E-05 6.85E-05 0.000

mg/dscm 7.09E-02 2.00E-02 7.60E-02 0.056

mg/dscm@7%O2 7.35E-02 2.11E-02 7.94E-02 0.058

Compound: Selenium

Average

RunNumber 1 2 3

Mass_mg 0.0067 0.0047 0.0053 0.006

Elb/hr 5.43E-03 3.78E-03 4.42E-03 0.005

lb/mmBtuO2 1.59E-06 1.15E-06 1.35E-06 0.000

mg/dscm 1.77E-03 1.27E-03 1.50E-03 0.002

mg/dscm@7%O2 1.84E-03 1.34E-03 1.57E-03 0.002

Location: Stack Exit - Method 6C

Friday, February 11, 2011 Page 18 of 33
Compound: Sulfur Dioxide

Average

Run 1 2 3

Elb/hr 3.22E+03 3.37E+03 3.55E+03 3,380.000

lb/mmBtuO2 9.50E-01 1.03E+00 1.06E+00 1.013

ppm 3.93E+02 4.24E+02 4.41E+02 419.333

ppm@7%O2 4.13E+02 4.47E+02 4.63E+02 441.000

Location: Stack Exit - Method 7E

Compound: Nitrogen oxides (NOx)

Average

Run 1 2 3

Elb/hr 1.19E+03 1.19E+03 1.23E+03 1,203.333

lb/mmBtuO2 3.53E-01 3.62E-01 3.69E-01 0.361

ppm 2.03E+02 2.08E+02 2.13E+02 208.000

ppm@7%O2 2.13E+02 2.19E+02 2.24E+02 218.667

Location: Stack Exit - OTM - 27/28

Compound: Filterable Particulate

Average

RunNumber 1 2 3

Mass_mg 85 93.2 195.6 124.600

Elb/hr 7.12E+01 8.94E+01 1.67E+02 109.200

gr/dscf 1.01E-02 1.31E-02 2.34E-02 0.016

gr/dscf@7%O2 1.06E-02 1.37E-02 2.46E-02 0.016

lb/mmBtuO2 2.09E-02 2.70E-02 4.86E-02 0.032

Compound: Filterable PM2.5

Average

RunNumber 1 2 3

Mass_mg 83.6 88.3 194.5 122.133

Elb/hr 7.00E+01 8.47E+01 1.66E+02 106.900

gr/dscf 9.91E-03 1.24E-02 2.33E-02 0.015

gr/dscf@7%O2 1.04E-02 1.30E-02 2.45E-02 0.016

lb/mmBtuO2 2.06E-02 2.56E-02 4.84E-02 0.032

Compound: Inorganic (Aqueous) Condensible Pa

Average

RunNumber 1 2 3

Mass_mg 48.3 32.8 24 35.033

Elb/hr 4.04E+01 3.15E+01 2.05E+01 30.800

gr/dscf 5.72E-03 4.61E-03 2.87E-03 0.004

gr/dscf@7%O2 6.02E-03 4.82E-03 3.02E-03 0.005

lb/mmBtuO2 1.19E-02 9.52E-03 5.97E-03 0.009

Compound: Organic Condensible Particulate

Average

RunNumber 1 2 3

Mass_mg 4.3 14.4 16.3 11.667

Elb/hr 3.60E+00 1.38E+01 1.39E+01 10.433

gr/dscf 5.10E-04 2.03E-03 1.95E-03 0.001

gr/dscf@7%O2 5.37E-04 2.12E-03 2.05E-03 0.002

Friday, February 11, 2011 Page 19 of 33
Process Run Data

lb/mmBtuO2 1.06E-03 4.18E-03 4.05E-03 0.003

Compound: Total Particulate

Average

RunNumber 1 2 3

Mass_mg 135.6 138.4 233.9 169.300

Elb/hr 1.14E+02 1.33E+02 2.00E+02 149.000

gr/dscf 1.61E-02 1.95E-02 2.80E-02 0.021

gr/dscf@7%O2 1.70E-02 2.04E-02 2.95E-02 0.022

lb/mmBtuO2 3.34E-02 4.02E-02 5.82E-02 0.044

Compound: Total PM2.5

Average

RunNumber 1 2 3

Mass_mg 134.2 133.5 232.8 166.833

Elb/hr 1.12E+02 1.28E+02 1.99E+02 146.333

gr/dscf 1.59E-02 1.88E-02 2.78E-02 0.021

gr/dscf@7%O2 1.67E-02 1.96E-02 2.93E-02 0.022

lb/mmBtuO2 3.31E-02 3.87E-02 5.79E-02 0.043

Friday, February 11, 2011 Page 20 of 33
Process Run Data

Run Name Value UOM Comments

Target

Value

1 Average Heat Input 2901 MMBtu/hr 0 RUN 1

2 Average Heat Input 0 MMBtu/hr 0

3 Average Heat Input 0 MMBtu/hr 0

1 Fuel Oil Firing Rate 18664 gal/hr 0 RUN 1

2 Fuel Oil Firing Rate 0 gal/hr 0

3 Fuel Oil Firing Rate 0 gal/hr 0

1 Flue Gas Flow Rate 814009 0 RUN 1

1 Flue Gas Oxygen Content 7.78 % 0 RUN 1

1 Flue Gas Carbon Dioxide Content 10.57 % 0 RUN 1

1 Flue Gas Moisture Content 10.12 % 0 RUN 1

1 Flue Gas Sampling Point Temperature 220 Deg F 0 RUN 1

1 Flue Gas Pressure 29.55 "Hg 0 RUN 1

1 Standard Pressure 29.92 "Hg 0 RUN 1

1 Standard Temperature 68 Deg F 0 RUN 1

1 Unit Gross Electrical Output 312 Mwe 0 RUN 1

1 Unit Net Electric Generation 287 MWh 0 RUN 1

4 Average Heat Input 2910 MMBtu/hr 0 RUN 2

4 Fuel Oil Firing Rate 18693 gal/hr 0 RUN 2

4 Flue Gas Flow Rate 797236 0 RUN 2

4 Flue Gas Oxygen Content 7.7 % 0 RUN 2

4 Flue Gas Carbon Dioxide Content 10.46 % 0 RUN 2

4 Flue Gas Moisture Content 10.21 % 0 RUN 2

4 Flue Gas Sampling Point Temperature 221 Deg F 0 RUN 2

4 Flue Gas Pressure 29.58 "Hg 0 RUN 2

4 Standard Pressure 29.92 "Hg 0 RUN 2

4 Standard Temperature 68 Deg F 0 RUN 2

4 Unit Gross Electrical Output 287 Mwe 0 RUN 2

4 Unit Net Electric Generation 312 MWh 0 RUN 2

5 Average Heat Input 2915 MMBtu/hr 0 RUN 3

5 Fuel Oil Firing Rate 18702 gal/hr 0 RUN 3

5 Flue Gas Flow Rate 802626 0 RUN 3

5 Flue Gas Oxygen Content 7.65 % 0 RUN 3

5 Flue Gas Carbon Dioxide Content 10.45 % 0 RUN 3

Friday, February 11, 2011 Page 21 of 33
APCD Run Data

Process Lab Run Data

5 Flue Gas Moisture Content 10.61 % 0 RUN 3

5 Flue Gas Sampling Point Temperature 224 Deg F 0 RUN 3

5 Flue Gas Pressure 29.59 "Hg 0 RUN 3

5 Standard Pressure 29.92 "Hg 0 RUN 3

5 Standard Temperature 68 Deg F 0 RUN 3

5 Unit Gross Electrical Output 312 Mwe 0 RUN 3

5 Unit Net Electric Generation 287 MWh 0 RUN 3

Run Name Value UOM Comments

1 Fuel Higher Heating Value 17700 Btu/lb

1 Fuel Moisture 0.070 %

1 Fuel Mercury Content 0.031 ppm

1 Fuel Cadmium Content 0.49 ppm

1 Fuel Nickel Content 4.5 ppm

1 Fuel Arsenic Content 2 ppm

1 Fuel Chromium Content 1.5 ppm

1 Fuel Beryllium Content 0.98 ppm

1 Fuel Lead Content 1.5 ppm

1 Fuel Manganese Content 1.5 ppm

1 Fuel Chlorine Content 61.6 ppm

1 Fuel Fluorine Content 150 ppm

1 Fuel Cobalt Content 0.28 ppm

1 Fuel Antimony Content 5.9 ppm

1 Fuel Phospohorous Content 5.6 ppm

1 Fuel Selenium Content 0.91 ppm

2 Fuel Higher Heating Value 17800 Btu/lb

2 Fuel Moisture 0.091 %

2 Fuel Mercury Content 0.032 ppm

2 Fuel Cadmium Content 0.47 ppm

2 Fuel Nickel Content 4.4 ppm

2 Fuel Arsenic Content 1.9 ppm

2 Fuel Chromium Content 1.4 ppm

2 Fuel Beryllium Content 0.94 ppm

2 Fuel Lead Content 1.4 ppm

2 Fuel Manganese Content 0.2 ppm

2 Fuel Chlorine Content 62.7 ppm

2 Fuel Fluorine Content 150 ppm

Friday, February 11, 2011 Page 22 of 33
2 Fuel Cobalt Content 0.3 ppm 2 Fuel Antimony Content 5.6 ppm 2 Fuel Phospohorous Content 4.8 ppm 2 Fuel Selenium Content 0.78 ppm 3 Fuel Higher Heating Value 17700 Btu/lb 3 Fuel Moisture 0.071 % 3 Fuel Mercury Content 0.031 ppm 3 Fuel Cadmium Content 0.42 ppm 3 Fuel Nickel Content 4.1 ppm 3 Fuel Arsenic Content 1.7 ppm 3 Fuel Chromium Content 1.3 ppm 3 Fuel Beryllium Content 0.85 ppm 3 Fuel Lead Content 1.3 ppm 3 Fuel Manganese Content 1.3 ppm 3 Fuel Chlorine Content 110 ppm 3 Fuel Fluorine Content 150 ppm 3 Fuel Cobalt Content 0.26 ppm 3 Fuel Antimony Content 5.1 ppm 3 Fuel Phospohorous Content 4.8 ppm 3 Fuel Selenium Content 0.67 ppm 4 Fuel Higher Heating Value 17600 Btu/lb 4 Fuel Moisture 0.089 % 4 Fuel Mercury Content 0.031 ppm 4 Fuel Cadmium Content 0.49 ppm 4 Fuel Nickel Content 6.3 ppm 4 Fuel Arsenic Content 2 ppm 4 Fuel Chromium Content 1.5 ppm 4 Fuel Beryllium Content 0.98 ppm 4 Fuel Lead Content 1.5 ppm 4 Fuel Manganese Content 1.5 ppm 4 Fuel Chlorine Content 114 ppm 4 Fuel Fluorine Content 150 ppm 4 Fuel Cobalt Content 0.32 ppm 4 Fuel Antimony Content 5.9 ppm 4 Fuel Phospohorous Content 4.8 ppm 4 Fuel Selenium Content 0.82 ppm 5 Fuel Higher Heating Value 17600 Btu/lb 5 Fuel Moisture 0.045 % 5 Fuel Mercury Content 0.031 ppm 5 Fuel Cadmium Content 0.46 ppm 5 Fuel Nickel Content 3.9 ppm 5 Fuel Arsenic Content 1.8 ppm 5 Fuel Chromium Content 1.4 ppm

Friday, February 11, 2011 Page 23 of 33
5 Fuel Beryllium Content 0.91 ppm

5 Fuel Lead Content 1.4 ppm

5 Fuel Manganese Content 1.4 ppm

5 Fuel Chlorine Content 110 ppm

5 Fuel Fluorine Content 150 ppm

5 Fuel Cobalt Content 0.26 ppm

5 Fuel Antimony Content 5.5 ppm

5 Fuel Phospohorous Content 4.8 ppm

5 Fuel Selenium Content 0.7 ppm

6 Fuel Higher Heating Value 17600 Btu/lb

6 Fuel Moisture 0.057 %

6 Fuel Mercury Content 0.033 ppm

6 Fuel Cadmium Content 0.44 ppm

6 Fuel Nickel Content 3.9 ppm

6 Fuel Arsenic Content 1.8 ppm

6 Fuel Chromium Content 1.3 ppm

6 Fuel Beryllium Content 0.88 ppm

6 Fuel Lead Content 1.3 ppm

6 Fuel Manganese Content 1.3 ppm

6 Fuel Chlorine Content 239 ppm

6 Fuel Fluorine Content 150 ppm

6 Fuel Cobalt Content 0.29 ppm

6 Fuel Antimony Content 5.3 ppm

6 Fuel Phospohorous Content 4.8 ppm

6 Fuel Selenium Content 0.69 ppm

Friday, February 11, 2011 Page 24 of 33
Sampling / Stack Data Results Detail

Location Stack Exit - Method 10

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 11, 2011 Page 25 of 33
Location Stack Exit - Method 23

Average

Run Number 1 2 3

Test Date 5/11/2010 5/12/2010 5/12/2010

Run Start Time 2:12:00 PM 7:25:00 AM 2:35:00 AM

Run Finish Time 11:50:00 PM 3:34:00 PM 1/1/1900 

2:15:00 AM

Net Traversing Points 50 49 49

Net Run Time, minutes 480 480 480

Nozzle Diameter, inches 0.206 0.206 0.206 0.206

Pitot Tube Coefficient 0.81 0.825 0.82 0.818

Dry Gas Meter Calibration Factor 0.985 0.989 0.989 0.988

Barometric Pressure, inches of Mercury 29.66 29.71 29.7 29.690

Average Orifice Meter Differential, inches H2O 1.52 1.54 1.32 1.460

Dry Gas Meter Volume Sampled, cubic feet 335.693 345.152 319.260 333.368

Average Dry Gas Meter Temperature, °F 90.82 96.61 97.23 94.887

Dry Gas Meter Volume Sampled, dscf 315.388 322.762 297.956 312.035

Total Moisture Liquid collected, g 668.6 753 713 711.533

Volume of Water Vapor, standard cubic feet 31.47 35.44 33.56 33.490

Moisture Content of Stack Gas, % 9.07 9.89 10.12 9.693

Moisture Saturation at Stack Gas Temperature, % 100.00 100.00 100.00 100.000

Dry Mole Fraction 0.9093 0.9011 0.8988 0.903

Carbon Dioxide, % 10.5 10.4 10.5 10.467

Oxygen, % 7.7 7.6 7.7 7.667

Carbon Monoxide & Nitrogen, % 81.8 82 81.8 81.867

Fuel Factor 1.26 1.28 1.26

Dry Molecular Weight, lb/lb-Mole 29.99 29.97 29.99 29.983

Wet Molecular weight, lb/lb-Mole 28.90 28.79 28.78 28.823

Flue Gas Static Pressure, inches of H2O -1.5 -1.4 -1.4 -1.433

Absolute Flue Gas Pressure, inches of Mercury 29.55 29.61 29.60 29.587

Average Stack Gas Temperature, °F 219.63 232.44 225.94 226.003

Average Velocity Head, inches of H2O 1.2273352792

3844

1.170103255

7261

1.119803964

52806

1.172

Average Stack Gas Velocity, feet/second 68.44 68.76 66.57 67.923

Stack Cross-Sectional Area, square feet 283.529 283.529 283.529 283.529

Dry Volumetric Flow Rate, dry scfm 812,312.6 795,401.1 775,118.8 794,277.500

Actual Wet Volumetric Flue Gas Flow Rate, acfm 1,164,283.5 1,169,727.2 1,132,471.5 1,155,494.0

67

Percent Isokinetic of Sampling Rate, % 99.1 103.6 98.1 100.267

Percent Excess Air, % 55.4 54.1 55.4 54.967

F-Factor, dscfm/MMBtu @ %O2 9190 9190 9190 9,190.000

Round Duct Diameter, inches 228 228 228

Rectangular Duct Width, inches 0 0 0

Rectangular Duct Length, inches 0 0 0

Fw 10320 10320 10320 10,320.000

Fc 1420 1420 1420 1,420.000

Friday, February 11, 2011 Page 26 of 33
Location Stack Exit - Method 25A

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 11, 2011 Page 27 of 33
Location Stack Exit - Method 29

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, February 11, 2011 Page 28 of 33
Location Stack Exit - Method 3A CO2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 11, 2011 Page 29 of 33
Location Stack Exit - Method 3A O2

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 11, 2011 Page 30 of 33
Location Stack Exit - Method 6C

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 11, 2011 Page 31 of 33
Location Stack Exit - Method 7E

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Carbon Dioxide, %

Oxygen, %

Fuel Factor

Dry Volumetric Flow Rate, dry scfm

F-Factor, dscfm/MMBtu @ %O2

Moisture, %

Analyzer Make

Analyzer Model

Analyzer Serial Number

Operating Range

Operating Units

No. Readings/Avg.

Calibration Set

Calibration Pre Zero Cylinder ID

Calibration Pre Zero Cylinder Instrument Response

Calibration Pre Zero Cylinder Bias

Calibration Pre Zero Cylinder Drift

Calibration Pre High Cylinder ID

Calibration Pre High Cylinder Instrument Response

Calibration Pre High Cylinder Bias

Calibration Pre High Cylinder Drift

Calibration Post Zero Cylinder ID

Calibration Post Zero Cylinder Instrument Response

Calibration Post Zero Cylinder Bias

Calibration Post Zero Cylinder Drift

Calibration Post High Cylinder ID

Calibration Post High Cylinder Instrument Response

Calibration Post High Cylinder Bias

Calibration Post High Cylinder Drift

Cavg

Cavg Units

Cgas

Cgas Units

Fuel Type

Fw

Fc

Cgasw

Cgasw Units

Friday, February 11, 2011 Page 32 of 33
Location Stack Exit - OTM - 27/28

Average

Run Number

Test Date

Run Start Time

Run Finish Time

Net Traversing Points

Net Run Time, minutes

Nozzle Diameter, inches

Pitot Tube Coefficient

Dry Gas Meter Calibration Factor

Barometric Pressure, inches of Mercury

Average Orifice Meter Differential, inches H2O

Dry Gas Meter Volume Sampled, cubic feet

Average Dry Gas Meter Temperature, °F

Dry Gas Meter Volume Sampled, dscf

Total Moisture Liquid collected, g

Volume of Water Vapor, standard cubic feet

Moisture Content of Stack Gas, %

Moisture Saturation at Stack Gas Temperature, %

Dry Mole Fraction

Carbon Dioxide, %

Oxygen, %

Carbon Monoxide & Nitrogen, %

Fuel Factor

Dry Molecular Weight, lb/lb-Mole

Wet Molecular weight, lb/lb-Mole

Flue Gas Static Pressure, inches of H2O

Absolute Flue Gas Pressure, inches of Mercury

Average Stack Gas Temperature, °F

Average Velocity Head, inches of H2O

Average Stack Gas Velocity, feet/second

Stack Cross-Sectional Area, square feet

Dry Volumetric Flow Rate, dry scfm

Actual Wet Volumetric Flue Gas Flow Rate, acfm

Percent Isokinetic of Sampling Rate, %

Percent Excess Air, %

F-Factor, dscfm/MMBtu @ %O2

Round Duct Diameter, inches

Rectangular Duct Width, inches

Rectangular Duct Length, inches

Fw

Fc

Friday, February 11, 2011 Page 33 of 33